Facility _Information

facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 56 189 PowerSouth Energy Cooperative PowerSouth Energy

Cooperative legal ownerP.O. Box 550 Andalusia AL 36420-1299

Page 1Facility _Information

plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Charles R. Lowman

4392 Carson Road

Leroy AL 36548 P.O. Box 10 Leroy AL 36548-0010

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas Don't Know TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Deviations must be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. Yes EPA CAMD and to the Alabam a Department of Environmental Management (ADEM) BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 4Facility _Information

BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 5Facility _Information

BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 6Facility _Information

BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 7Facility _Information

BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 8Facility _Information

BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 9Facility _Information

BOILER INFORMATION SCREEN1) Work around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 10Facility _Information

BOILER INFORMATION SCREEN1) Work around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 11Facility _Information

BOILER INFORMATION SCREEN1) Work around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 12Facility _Information

BOILER INFORMATION SCREEN1) Work around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 13Facility _Information

BOILER INFORMATION SCREEN1) Work around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 14Facility _Information

BOILER INFORMATION SCREEN1) W ork around for value >300 rejected by certain cells as provided in EPA's document titled "Electrical Utilities MACT ICR - FAQ," Question # EICR-020, p. 14. Design Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Operating Steam Temperatures (Degrees F.)Unit 1 = 950Unit 2 = 1,000Unit 3 = 1,000Design Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,000Operating Steam Reheat Temperature (Degrees F.)Unit 1 = N/AUnit 2 = 1,000Unit 3 = 1,0002) Design heat input and present maximum heat input descriptive values taken from the facility's Title V Major Source Operating Permit title page.3) PowerSouth has no active plan to retire any of the units at this facility.BOILER FUELS SCREEN 1) Fuel oil is only used for start up and flame stabilization for all three units at this plant and represents ~0.25% of annual unit fuel burn in any given year. 2) No analyses available: all fuel oil

Page 15facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 56 1 Environm ental Compliance Specialist Larry J. Spann 3344273254

3348180651

larry.spann@powersouth.com

TRUE 56 2 Plant Supervisor - Environmental Results Donald Dorman

2512468132

2512468000

don.dorman@powersouth.com

FALSE

Page 16facility _coal_utilized

facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 56 bitum inous 100 100

Page 17facility _oil_utilized

facility _id oil_type percentage_volume percentage_btu

other_type 56 No.2 Fuel Oil (distillate)

100 100

Page 18facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 19facility _other_materials

rcra_explain

Page 20boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MW e_capacity 56 1 Wa ll firing - front firing Dry Bottom coal 905 905 86 56 2 Wa ll firing - opposed firing Dry Bottom coal 2500 2500 258 56 3 Wa ll firing - opposed firing Dry Bottom coal 2500 2500 258

Page 21boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 78 89 89 1250 1250 1 1 FALSE 1 232 88 86 1800 1800 1 1 FALSE 1 232 88 86 1800 1800 1 1 FALSE 1

Page 22boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1 7776 73 N FALSE FALSE 1 6852 65.6 Subpart D FALSE FALSE 1 7882 75.3 Subpart D FALSE

Page 23boiler_information

NOx_control

SO2_control

combustion_additives Yes No No No No No No No No

Page 24boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 56 1 coal - bituminous2007 99.75 99.75 56 1 coal - bituminous2008 99.75 99.75 56 1 coal - bituminous2009 99.75 99.75 56 1 oil - distillate 2007 0.25 0.25 56 1 oil - distillate 2008 0.25 0.25 56 1 oil - distillate 2009 0.25 0.25 56 2 coal - bituminous2007 99.75 99.75 56 2 coal - bituminous2008 99.75 99.75 56 2 coal - bituminous2009 99.75 99.75 56 2 oil - distillate 2007 0.25 0.25 56 2 oil - distillate 2008 0.25 0.25 56 2 oil - distillate 2009 0.25 0.25 56 3 coal - bituminous2007 99.75 99.75 56 3 coal - bituminous2008 99.75 99.75 56 3 coal - bituminous2009 99.75 99.75 56 3 oil - distillate 2007 0.25 0.25 56 3 oil - distillate 2008 0.25 0.25 56 3 oil - distillate 2009 0.25 0.25

Page 25boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 56 1 Low NOx Burner 3/1/2000

Page 26boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online

Page 27boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 28facility _units

facility _id unit_id 56 1 56 2 56 3

Page 29unit_boilers

facility _id unit_id boiler_id 56 1 1 56 2 2 56 3 3

Page 30facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 56 1PM PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 6/1/1974 56 2PM PM control Electrostatic precipitator, hot side, w/o flue gas conditioning FALSE 6/1/1978 56 3PM PM control Electrostatic precipitator, hot side, w/o flue gas conditioning FALSE 6/1/1980 56 JBR-1/2 SO2 control Jet Bubbling Reactor FALSE 12/1/2007 56 SCR-2 NOx control Selective Cataly

tic Reduction FALSE 12/1/2007 Other (specify) 56 SCR-3 NOx control Selective Cataly

tic Reduction FALSE 12/1/2007 Other (specify) 56 ST-03C SO2 control Spray type FALSE 6/1/1978 56 ST-03D SO2 control Spray type FALSE 6/1/1980 56 ST-2 SO2 control Spray type FALSE 6/1/1978 56 ST-3 SO2 control Spray type FALSE 6/1/1980

Page 31facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Lim estone No Anhydrous Ammonia Anhydrous Ammonia Lim estone No Lim estone No Lim e No Lim e No

Page 32facility _sampling_ports

facility _id sampling_port_id 56 SP-3 56 SP-CS004 56 SP-MS001 56 SP-MS03C 56 SP-MS03D

Page 33facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 56 CS004 415 18.2 63 56 MS001 250 13 35 56 MS03C 399 16.5 28.6 56 MS03D 399 16.5 28.6

Page 34configurations

facility _id configuration_id 56 1 56 1B 56 2 56 2B 56 3 56 3C 56 3D

Page 35configuration_components

facility _id configuration_id

component_id

order component_type port_near 56 1 1 1 Unit 56 1 1PM 2 PM control 56 1 CS004 5 Stack 56 1 JBR-1/2 3 SO2 control 56 1 SP-CS004 4 Sam pling Port next 56 1B 1 1 Unit 56 1B 1PM 2 PM control 56 1B MS001 4 Stack 56 1B SP-MS001 3 Sam pling Port next 56 2 2 1 Unit 56 2 2PM 2 PM control 56 2 CS004 6 Stack 56 2 JBR-1/2 4 SO2 control 56 2 SCR-2 3 NOx control 56 2 SP-CS004 5 Sam pling Port next 56 2B 2 1 Unit 56 2B 2PM 2 PM control 56 2B MS03C 5 Stack 56 2B SP-MS03C 4 Sam pling Port next 56 2B ST-03C 3 SO2 control 56 3 3 1 Unit 56 3 3PM 2 PM control 56 3 MS03D 5 Stack 56 3 SP-MS03D 4 Sam pling Port next 56 3 ST-03D 3 SO2 control 56 3C 3 1 Unit 56 3C 3PM 2 PM control 56 3C MS03C 6 Stack 56 3C SCR-3 3 NOx control 56 3C SP-MS03C 5 Sam pling Port next 56 3C ST-03C 4 SO2 control 56 3D 3 1 Unit 56 3D 3PM 2 PM control 56 3D MS03D 6 Stack 56 3D SCR-3 3 NOx control 56 3D SP-MS03D 5 Sam pling Port next 56 3D ST-03D 4 SO2 control

Page 36configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 56 1B PM (Filterable) Fderal - Title V Operating Permit

0.12 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 1B Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.46 pound per million British Thermal Unit (lb/MMBtu) 56 1B Sulfur Dioxide (SO2) Federal - Title V Operating Permit

4 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

1 hour 0.46 pound per million British Thermal Unit (lb/MMBtu) 56 1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 1 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 2 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

1 hour 0.46 pound per million British Thermal Unit (lb/MMBtu) 56 2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 3C PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 3C Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

1 hour 0.46 pound per million British Thermal Unit (lb/MMBtu) 56 3C Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 3D PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 3D Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

1 hour 0.46 pound per million British Thermal Unit (lb/MMBtu) 56 3D Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 2B PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 2B Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

1 hour 0.5 pound per million British Thermal Unit (lb/MMBtu) 56 2B Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 3 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 56 3 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

1 hour 0.5 pound per million British Thermal Unit (lb/MMBtu) 56 3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

1 hour

Page 37configuration_pollutants1

avg_period_2

em lim it_details

test_method

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping EPA Method 17 See Notes Screen. Annual Stack Test

Test reports available at Plant site and Corporate Office; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) This unit only has an annual average limit = 0.46 lbs NOx / MMBtu. See Notes Screen.

Continuous Emissions Monitoring Systems (CEMS)

Minute and hourly

emissions data available for all unit operating time; 3 year records retention time. See Notes Screen.

CEMS Minute and hourly emissions data avalilable for all unit operating time; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) 0.46 lbs/MMBtu = annual average; 0.7 lbs/MMBtu = state requirement See Notes Screen.

Continuous Emissions Monitoring System (CEMS)

Minute and hourly

data available for all unit operation time; 3 year records retention time. 0.076 pound per hour (lb/hr)

No CEMS Minute and hourly emissions data available for all unit operation time; 3 year record retention time. EPA Reference Method 5 See Notes Screen. Annual stack test

Test reports kept on hand at the Plant and in Corporate Office; 3 year records retention time. EPA Method 5 See Notes Screen. Annual stack test

Copy of test report kept at Plant and Corporate office; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) 0.46 lbs/MMBtu = annual average 0.06 pound per million British Thermal Unit (lb/MMBtu)

No Continuous Emissions Monitoring (CEMS) Minute and hourly

emissions data available for all operating times; 3 year records retention time. 0.076 pound per million British Thermal Unit (lb/MMBtu)

No CEMS Minute and hourly emissions data available for all operating times; 3 year records retention time. EPA Reference Method 5 See Notes Screen. Annual stack test

Copy of test report kept at Plant and Corporate Office; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) 0.46 lbs/MMBtu = annual average 0.06 pound per million British Thermal Unit (lb/MMBtu)

No Continuous Emissions Monitoring System (CEMS) Minute and hourly

emissions data available for all operating time; 3 year records retention time. 0.29 pound per million British Thermal Unit (lb/MMBtu)

No CEMS Minute and hourly emissions data available for all operating time; 3 year records retention time. EPA Reference Method 5 See Notes Screen. Annual stack test

Copy of test report kept at Plant and Corporate Office; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) 0.46 lbs/MMBtu = annual average 0.06 pound per million British Thermal Unit (lb/MMBtu)

No Continuous Emissions Monitoring System (CEMS) Copy of test report kept at Plant and Corporate Office; 3 year records retention time. 0.29 pound per million British Thermal Unit (lb/MMBtu)

No CEMS Copy of test report kept at Plant and Corporate Office; 3 year records retention time. EPA Method 5 See Notes Screen. Annual filterable particulate stack test

Test reports available at the Plant and Corporate Office; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) 0.5 Lbs/MMBtu = annual average prior to 1/1/2008. See Notes Screen. Continuous Emissions Monitoring System (CEMS)

Minute and hourly

emissions data available for all unit operating time; 3 year records retention time. See Notes Screen.

CEMS Minute and hourly emissions data available for all unit operating time; 3 year records retention time. EPA Method 5 See Notes Screen. Annual filterable particulate stack test

Test reports available at the Plant and Corporate Office; 3 year records retention time. pound per million British Thermal Unit (lb/MMBtu) 0.5 lbs/MMBtu = annual average prior to 1/1/2008. See Notes Screen. Continuous Emissions Monitoring System (CEMS)

Hourly and minute data available for all unit operating time; 3 year records retention time. See Notes Screen.

CEMS Hourly

and minute data available for all unit operating time; 3 year records retention time.

Page 38configuration_pollutants1

req_reporting Test reports submitted to the Alabama Department of Environmental Management (ADEM). Quarterly

electronic data report to US EPA CAMD and to ADEM. Quarterly

electronic data report to US EPA CAMD and to ADEM. Quarterly

electronic data reports to US EPA CAMD and to ADEM. Quarterly

electronic data reports to US EPA CAMD and to ADEM. Test report submitted to the Alabama Department of Environmental Management (ADEM). Test report submitted to the Alabama Department of Environmental Management (ADEM). Quarterly

electronic data report submitted to the US EPA CAMD and ADEM. Quarterly

electronic data report submitted to US EPA and ADEM. Test report submitted to the Alabama Department of Environmental Management (ADEM). Quarterly

electronic data report submitted to US EPA CAMD and ADEM. Quarterly

electronic data report submitted to US EPA CAMD and ADEM. Test report submitted to the Alabama Department of Environmental Management (ADEM). Quarterly

electronic data report submitted to US EPA CAMD and ADEM. Quarterly

electronic data report submitted to US EPA CAMD and ADEM. Report submitted to the Alabama Department of Environmental Management (ADEM). Quarterly

electronic data report submitted to ADEM and EPA Region 4. Quarterly

electronic data report submitted to ADEM and EPA Region 4. Report submitted to the Alabama Department of Environmental Management (ADEM). Quarterly

electronic data report submitted to ADEM and EPA Region 4. Quarterly

electronic data report submitted to ADEM and EPA Region 4.

Page 39control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 40control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 41control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 42control_technologies

feed_rate_units

Page 43control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 44control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 45control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 46control_costs

CBI

Page 47misc_controls

facility _id misc_control_id

control_description

Page 48misc_control_configurations

facility _id misc_control_id

configuration_id

Page 49fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 56 Alliance - 1 1/1/2009 50347.16 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 10

10/1/2009 62083.88 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 11 11/1/2009 71210.24 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 1212/1/2009 77709.62 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 2 2/1/2009 62290.6 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 3 3/1/2009 49026.27 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 4 4/1/2009 45433.8 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 5 5/1/2009 73246.1 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 6 6/1/2009 40256.9 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 7 7/1/2009 49236.04 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 8 8/1/2009 37072.35 short tons (2000 lbs) coal IN IN - Gibson 56 Alliance - 9 9/1/2009 12419.83 short tons (2000 lbs) coal IN IN - Gibson 56 Am erican - 1 1/1/2009 33109 short tons (2000 lbs) coal IL IL - Gallatin 56 Am erican - 2 2/1/2009 24189.75 short tons (2000 lbs) coal IL IL - Gallatin 56 Am erican - 3 3/1/2009 27190 short tons (2000 lbs) coal IL IL - Gallatin 56 Am erican - 4 4/1/2009 24164.4 short tons (2000 lbs) coal IL IL - Gallatin 56 Am erican - 5 5/1/2009 36048.57 short tons (2000 lbs) coal IL IL - Gallatin 56 Am erican - 7 7/1/2009 24462.07 short tons (2000 lbs) coal IL IL - Gallatin 56 Bum pers - 1 1/1/2009 387.21 barrels oil AL AL - W ashington 56 Bum pers - 10

10/1/2009 2695.31 barrels oil AL AL - W ashington 56 Bum pers - 11

11/1/2009 1626.62 barrels oil AL AL - W ashington 56 Bum pers - 12

12/1/2009 3661.95 barrels oil AL AL - W ashington 56 Bum pers - 2 2/1/2009 2174.41 barrels oil AL AL - W ashington 56 Bum pers - 3 3/1/2009 2155.05 barrels oil AL AL - W ashington 56 Bum pers - 4 4/1/2009 714.48 barrels oil AL AL - W ashington 56 Bum pers - 5 5/1/2009 1975.83 barrels oil AL AL - W ashington 56 Bum pers - 6 6/1/2009 1414.67 barrels oil AL AL - W ashington 56 Bum pers - 7 7/1/2009 1458 barrels oil AL AL - W ashington 56 Bum pers - 8 8/1/2009 899.45 barrels oil AL AL - W ashington 56 Bum pers - 9 9/1/2009 899.14 barrels oil AL AL - W ashington 56 Cheveron - 2 2/1/2009 41640.3 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 10

10/1/2009 41347.8 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 11

11/1/2009 22468.6 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 12

12/1/2009 44076.2 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 3 3/1/2009 55894.6 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 4 4/1/2009 35741.8 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 5 5/1/2009 28857.6 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 6 6/1/2009 34486.1 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 7 7/1/2009 20827.4 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 8 8/1/2009 35806.5 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron - 9 9/1/2009 36344.7 short tons (2000 lbs) coal AL AL - Fayette 56 Chevron -1 1/1/2009 54727.3 short tons (2000 lbs) coal AL AL - Fayette 56 Davison - 1 1/1/2009 358.05 barrels oil AL AL - Mobile 56 InterOcean - 1

/1/2009 40395.33 short tons (2000 lbs) coal Other Colum bia, South Am erica 56 Pepco - 12 12/1/2009 1447.24 barrels oil AL AL - Mobile 56 Pepco - 4 4/1/2009 719.57 barrels oil AL AL - Mobile 56 Pepco - 7 7/1/2009 170.67 barrels oil AL AL - Mobile 56 Pepco - 8 8/1/2009 356.88 barrels oil AL AL - Mobile 56 Twin Pines - 2

2/1/2009 39047 short tons (2000 lbs) coal AL AL - W alker 56 Twin Pines - 3

3/1/2009 32389.63 short tons (2000 lbs) coal AL AL - W alker 56 Twin Pines - 4

4/1/2009 3165.35 short tons (2000 lbs) coal AL AL - W alker

Page 50fuel_shipments

56 Twin Pines - 5

5/1/2009 38746.28 short tons (2000 lbs) coal AL AL - W alker 56 Twin Pines - 6

6/1/2009 12843.06 short tons (2000 lbs) coal AL AL - W alker 56 Wi lliam son - 1

1/1/2009 12078 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 10

12/1/2009 12129 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 11

11/1/2009 12092 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 12

12/1/2009 12193 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 3

1/1/2009 24098 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 4

4/1/2009 12040 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 5

5/1/2009 36196 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 6

6/1/2009 36129 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 7

7/1/2009 24095 short tons (2000 lbs) coal IL IL - W illiam son 56 Wi lliam son - 8

8/1/2009 12143.05 short tons (2000 lbs) coal IL IL - W illiam son

Page 51fuel_shipments

coal_seam shipment_method Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge Springfield # 5

Barge IL # 5 Barge Ilinois # 5 Barge Illinois # 5 Barge Illinois # 5 Barge Illinois # 5 Barge Illinois # 5 Barge AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks AL - W ashington Trucks

Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train Pratt Unit Train AL - Mobile Trucks

La Loma mine

Barge AL - Mobile Trucks AL - Mobile Trucks AL - Mobile Trucks AL - Mobile Trucks

Pratt Barge Pratt Barge Pratt Barge

Page 52fuel_shipments

Pratt Barge Pratt Barge IL # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge Illinois # 6 Barge

Page 53fuel_shipment_configurations

facility _id shipment_id

configuration_id 56 Alliance - 1 1 56 Alliance - 1 1B 56 Alliance - 1 2 56 Alliance - 1 3C 56 Alliance - 1 3D 56 Alliance - 10

1 56 Alliance - 10

1B 56 Alliance - 10

2 56 Alliance - 10

3C 56 Alliance - 10

3D 56 Alliance - 11

1 56 Alliance - 11

1B 56 Alliance - 11

2 56 Alliance - 11

3C 56 Alliance - 11

3D 56 Alliance - 12

1 56 Alliance - 12

1B 56 Alliance - 12

2 56 Alliance - 12

3C 56 Alliance - 12

3D 56 Alliance - 2 1 56 Alliance - 2 1B 56 Alliance - 2 2 56 Alliance - 2 3D 56 Alliance - 3 1 56 Alliance - 3 1B 56 Alliance - 3 2 56 Alliance - 3 3C 56 Alliance - 3 3D 56 Alliance - 4 1 56 Alliance - 4 1B 56 Alliance - 4 2 56 Alliance - 4 3C 56 Alliance - 4 3D 56 Alliance - 5 1 56 Alliance - 5 1B 56 Alliance - 5 2 56 Alliance - 5 3C 56 Alliance - 5 3D 56 Alliance - 6 1 56 Alliance - 6 1B 56 Alliance - 6 2 56 Alliance - 6 3C 56 Alliance - 6 3D 56 Alliance - 7 1 56 Alliance - 7 1B 56 Alliance - 7 2 56 Alliance - 7 3C 56 Alliance - 7 3D 56 Alliance - 8 1 56 Alliance - 8 1B

Page 54fuel_shipment_configurations

56 Alliance - 8 2 56 Alliance - 8 3C 56 Alliance - 8 3D 56 Alliance - 9 1 56 Alliance - 9 1B 56 Alliance - 9 2 56 Alliance - 9 3C 56 Alliance - 9 3D 56 Am erican - 1 56 Am erican - 1

B 56 Am erican - 1

2 56 Am erican - 1

3C 56 Am erican - 1

3D 56 Am erican - 2

1 56 Am erican - 2

1B 56 Am erican - 2 56 Am erican - 2

3C 56 Am erican - 2

3D 56 Am erican - 3

1 56 Am erican - 3

1B 56 Am erican - 3

2 56 Am erican - 3

C 56 Am erican - 3

D 56 Am erican - 4

1 56 Am erican - 4

1B 56 Am erican - 4

2 56 Am erican - 4

3C 56 Am erican - 4

3D 56 Am erican - 5

1 56 Am erican - 5

1B 56 Am erican - 5

2 56 Am erican - 5

3D 56 Am erican - 7

1 56 Am erican - 7

1B 56 Am erican - 7

2 56 Am erican - 7

3C 56 Am erican - 7

3D 56 Bum pers - 1

1 56 Bum pers - 1

1B 56 Bum pers - 1

2 56 Bum pers - 1

3C 56 Bum pers - 1

3D 56 Bum pers - 10

1 56 Bum pers - 10

1B 56 Bum pers - 10

2 56 Bum pers - 10

3C 56 Bum pers - 10

3D 56 Bum pers - 11

1 56 Bum pers - 11

1B 56 Bum pers - 11

2 56 Bum pers - 11

3C 56 Bum pers - 11

3D

Page 55fuel_shipment_configurations

56 Bum pers - 12

1 56 Bum pers - 12

1B 56 Bum pers - 12

2 56 Bum pers - 12

3C 56 Bum pers - 12

3D 56 Bum pers - 2

1 56 Bum pers - 2

1B 56 Bum pers - 2

2 56 Bum pers - 2

3C 56 Bum pers - 2

3D 56 Bum pers - 3

1 56 Bum pers - 3

1B 56 Bum pers - 3

2 56 Bum pers - 3

3C 56 Bum pers - 3

3D 56 Bum pers - 4

1 56 Bum pers - 4

1B 56 Bum pers - 4

2 56 Bum pers - 4

3C 56 Bum pers - 4

3D 56 Bum pers - 5

1 56 Bum pers - 5

1B 56 Bum pers - 5

2 56 Bum pers - 5

3C 56 Bum pers - 5

3D 56 Bum pers - 6

1 56 Bum pers - 6

1B 56 Bum pers - 6

2 56 Bum pers - 6

3C 56 Bum pers - 6

3D 56 Bum pers - 7

1 56 Bum pers - 7

1B 56 Bum pers - 7

2 56 Bum pers - 7

3C 56 Bum pers - 7

3D 56 Bum pers - 8

1 56 Bum pers - 8

1B 56 Bum pers - 8

2 56 Bum pers - 8

3C 56 Bum pers - 8

3D 56 Bum pers - 9

1 56 Bum pers - 9

1B 56 Bum pers - 9

2 56 Bum pers - 9

3C 56 Bum pers - 9

3D 56 Cheveron - 2

1 56 Cheveron - 2

1B 56 Cheveron - 2

2 56 Cheveron - 2

3C 56 Cheveron - 2

3D 56 Chevron - 10

1 56 Chevron - 10

1B

Page 56fuel_shipment_configurations

56 Chevron - 10

2 56 Chevron - 10

3C 56 Chevron - 10

3D 56 Chevron - 11

1 56 Chevron - 11

1B 56 Chevron - 11

2 56 Chevron - 11

3C 56 Chevron - 11

3D 56 Chevron - 12

1 56 Chevron - 12

1B 56 Chevron - 12

2 56 Chevron - 12

3C 56 Chevron - 12

3D 56 Chevron - 31 56 Chevron - 31B 56 Chevron - 3

2 56 Chevron - 3

3D 56 Chevron - 41 56 Chevron - 41B 56 Chevron - 4

2 56 Chevron - 4

3C 56 Chevron - 4

3D 56 Chevron - 51 56 Chevron - 51B 56 Chevron - 5

2 56 Chevron - 5

3C 56 Chevron - 5

3D 56 Chevron - 61 56 Chevron - 61B 56 Chevron - 6

2 56 Chevron - 6

3C 56 Chevron - 6

3D 56 Chevron - 71 56 Chevron - 71B 56 Chevron - 7

2 56 Chevron - 7

3C 56 Chevron - 7

3D 56 Chevron - 81 56 Chevron - 81B 56 Chevron - 8

2 56 Chevron - 8

3C 56 Chevron - 8

3D 56 Chevron - 91 56 Chevron - 91B 56 Chevron - 9

2 56 Chevron - 9

3C 56 Chevron - 9

3D 56 Chevron -1 1 56 Chevron -1 1B 56 Chevron -1 2 56 Chevron -1 3C 56 Chevron -1 3D

Page 57fuel_shipment_configurations

56 Davison - 1 1 56 Davison - 1 1B 56 Davison - 1 2 56 Davison - 1 3C 56 Davison - 1 3D 56 InterOcean - 1

1 56 InterOcean - 1

1B 56 InterOcean - 1

2 56 InterOcean - 1

3C 56 InterOcean - 1

3D 56 Pepco - 12 1 56 Pepco - 12 1B 56 Pepco - 12 2 56 Pepco - 12 3C 56 Pepco - 12 3D 56 Pepco - 4 1 56 Pepco - 4 1B 56 Pepco - 4 2 56 Pepco - 4 3C 56 Pepco - 4 3D 56 Pepco - 7 1 56 Pepco - 7 1B 56 Pepco - 7 2 56 Pepco - 7 3C 56 Pepco - 7 3D 56 Pepco - 8 1 56 Pepco - 8 1B 56 Pepco - 8 2 56 Pepco - 8 3C 56 Pepco - 8 3D 56 Twin Pines - 2

1 56 Twin Pines - 2

1B 56 Twin Pines - 2

2 56 Twin Pines - 2

3C 56 Twin Pines - 2

3D 56 Twin Pines - 3

1 56 Twin Pines - 3

1B 56 Twin Pines - 3

2 56 Twin Pines - 3

3C 56 Twin Pines - 3

3D 56 Twin Pines - 4

1 56 Twin Pines - 4

1B 56 Twin Pines - 4

2 56 Twin Pines - 4

3C 56 Twin Pines - 4

3D 56 Twin Pines - 5

1 56 Twin Pines - 5

1B 56 Twin Pines - 5

2 56 Twin Pines - 5

3C 56 Twin Pines - 5

3D 56 Twin Pines - 6

1 56 Twin Pines - 6

1B

Page 58fuel_shipment_configurations

56 Twin Pines - 6

2 56 Twin Pines - 6

3C 56 Twin Pines - 6

3D 56 Wi lliam son - 1

1 56 Wi lliam son - 1

1B 56 Wi lliam son - 1

2 56 Wi lliam son - 1

3C 56 Wi lliam son - 1

3D 56 Wi lliam son - 10

1 56 Wi lliam son - 10

1B 56 Wi lliam son - 10

2 56 Wi lliam son - 10

3C 56 Wi lliam son - 10

3D 56 Wi lliam son - 11

1 56 Wi lliam son - 11

1B 56 Wi lliam son - 11

2 56 Wi lliam son - 11

3C 56 Wi lliam son - 11

3D 56 Wi lliam son - 12

1 56 Wi lliam son - 12

1B 56 Wi lliam son - 12

2 56 Wi lliam son - 12

3C 56 Wi lliam son - 12

3D 56 Wi lliam son - 3

1 56 Wi lliam son - 3

1B 56 Wi lliam son - 3

2 56 Wi lliam son - 3

3C 56 Wi lliam son - 3

3D 56 Wi lliam son - 4

1 56 Wi lliam son - 4

1B 56 Wi lliam son - 4

2 56 Wi lliam son - 4

3C 56 Wi lliam son - 4

3D 56 Wi lliam son - 5

1 56 Wi lliam son - 5

1B 56 Wi lliam son - 5

2 56 Wi lliam son - 5

3C 56 Wi lliam son - 5

3D 56 Wi lliam son - 6

1 56 Wi lliam son - 6

1B 56 Wi lliam son - 6

2 56 Wi lliam son - 6

3C 56 Wi lliam son - 6

3D 56 Wi lliam son - 7

1 56 Wi lliam son - 7

1B 56 Wi lliam son - 7

2 56 Wi lliam son - 7

3C 56 Wi lliam son - 7

3D 56 Wi lliam son - 8

1 56 Wi lliam son - 8

1B 56 Wi lliam son - 8

2 56 Wi lliam son - 8

3C

Page 59fuel_shipment_configurations

56 Wi lliam son - 8

3D

Page 60fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 56 Alliance - 1 2007-968-2 534018 tons 1.6 7.07 13534 Btu/gal 56 Alliance - 10

N/A 56 Alliance - 11

N/A 56 Alliance - 12

N/A 56 Alliance - 2 N/A 56 Alliance - 3 N/A 56 Alliance - 4 N/A 56 Alliance - 5 N/A 56 Alliance - 6 N/A 56 Alliance - 7 N/A 56 Alliance - 8 N/A 56 Alliance - 9 N/A 56 Am erican - 1

511-0812084-001

149101 tons 1.71 7.46 13625 Btu/lb 56 Am erican - 2

N/A 56 Am erican - 3

N/A 56 Am erican - 4

N/A 56 Am erican - 5

N/A 56 Am erican - 7

N/A 56 Bum pers - 1

N/A 56 Bum pers - 10

N/A 56 Bum pers - 11

N/A 56 Bum pers - 12

N/A 56 Bum pers - 2

N/A 56 Bum pers - 3

N/A 56 Bum pers - 4

N/A 56 Bum pers - 5

N/A 56 Bum pers - 6

N/A 56 Bum pers - 7

N/A 56 Bum pers - 8

N/A 56 Bum pers - 9

N/A 56 Cheveron - 2

N/A 56 Chevron - 10

N/A 56 Chevron - 11

N/A 56 Chevron - 12

N/A 56 Chevron - 3

N/A 56 Chevron - 4

N/A 56 Chevron - 5

N/A 56 Chevron - 6

N/A 56 Chevron - 7

N/A 56 Chevron - 8

N/A 56 Chevron - 9

N/A 56 Chevron -1 511-0819187-001 419478 tons 2.55 11.66 13244 Btu/lb 56 Davison - 1 N/A 56 InterOcean - 1

N/A 56 Pepco - 12 N/A 56 Pepco - 4 N/A 56 Pepco - 7 N/A 56 Pepco - 8 N/A 56 Twin Pines - 2

N/A 56 Twin Pines - 3

N/A 56 Twin Pines - 4

N/A

Page 61fuel_shipment_samples

56 Twin Pines - 5

N/A 56 Twin Pines - 6

N/A 56 Wi lliam son - 1

467027 170802 tons 2.7 10.63 13123 Btu/lb 56 Wi lliam son - 10

N/A 56 Wi lliam son - 11

N/A 56 Wi lliam son - 12

N/A 56 Wi lliam son - 3

N/A 56 Wi lliam son - 4

N/A 56 Wi lliam son - 5

N/A 56 Wi lliam son - 6

N/A 56 Wi lliam son - 7

N/A 56 Wi lliam son - 8

N/A

Page 62fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address 0.23 percent (dry) (%)

0.003 percent (dry) (%)

standard operational procedures Fuel supplier

Gibson County

Coal, LLC RR # 3, Box 235

0.36 percent (dry) (%) standard operational procedures Fuel supplier

The American Coal Company

101 Properous Place, Suite 125

0.02 percent (dry) (%) standard operational procedures Fuel supplier

Chevron Mining, Inc.Chevron Mining , Inc.

116 Inverness Drive East, Suite 207

Page 63fuel_shipment_samples

standard operational procedures Fuel supplier

Wi lliam son Energy, LLC

Pond Creek #1 MineP.O. Box 300

Page 64fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Princeton IN 47670 Standard Laboratories, Inc. 1530 N. Cullen Avenue

Evansville IN 47715 No

Lexington KY 40509 SGS North America, Inc. 618 Bob Posey

Steet Henderson KY 42419 No

Englewood CO 80112 SGS North America, Inc. 618 Bob Posey

Steet Henderson KY 42419 No

Page 65fuel_shipment_samples

Johnston City

IL 62951 Precision Testing Laboratory P.O. Box 1985

Beckley WV 25802 No

Page 66fuel_shipment_samples

analysis_copies

Page 67fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 56 Alliance - 1 2007-968-2Antim ony (Sb) 1.83 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Arsenic (As) 20 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Beryllium(Be) 2.4 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Cadmium (Cd) 0.12 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Chromium (Cr) 13 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Cobalt (Co) 6.9 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Copper (Cu) 7 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Fluoride (F) 34 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Lead (Pb) 23.3 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Manganese (Mn) 11 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Mercury (Hg) 11 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Molybdenum(Mo) 1.3 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Nickel (Ni) 24 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Selenium(Se) 1.5 mi crogram per gram (dry) (mg/g) FALSE 56 Alliance - 1 2007-968-2Vanadium(V) 18 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Antim ony

(Sb) 1 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Arsenic (As) 13 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Barium(Ba) 28 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Beryllium(Be) 1.1 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Cadmium (Cd) 0.2 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Chromium (Cr) 10 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Cobalt (Co) 5 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Copper (Cu) 6 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Lead (Pb) 34 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Manganese (Mn) 16 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Mercury (Hg) 0.12 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Molybdenum(Mo) 2 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Nickel (Ni) 17 mi crogram per gram (dry) (mg/g) FALSE 56 Am erican - 1

511-0812084-001

Vanadium(V) 15 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Arsenic (As) 11 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Barium(Ba) 203 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Beryllium(Be) 1.5 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Cadmium (Cd) 0.3 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Chromium (Cr) 24 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Cobalt (Co) 7 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Lead (Pb) 8 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Manganese (Mn) 30 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Mercury (Hg) 0.13 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Nickel (Ni) 16 mi crogram per gram (dry) (mg/g) FALSE 56 Chevron -1 511-0819187-001 Selenium(Se) 3 mi crogram per gram (dry) (mg/g) FALSE 56 Wi lliam son - 1

467027 Antim ony

(Sb) mi lligramper kilogram (dry) (mg/kg) TRUE 3 56 Wi lliam son - 1

467027 Arsenic (As) 3.83 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Barium(Ba) 87.7 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Beryllium(Be) 0.661 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Cadmium (Cd) 0.956 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Chromium (Cr) 4.45 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Cobalt (Co) 3.46 mi crogram per gram (dry) (mg/g) FALSE 56 Wi lliam son - 1

467027 Copper (Cu) 7.73 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Fluoride (F) mi lligramper kilogram (dry) (mg/kg) TRUE 10 56 Wi lliam son - 1

467027 Lead (Pb) 14.6 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Manganese (Mn) 40.6 mi lligramper kilogram (dry) (mg/kg) FALSE

Page 68fuel_sample_pollutants

56 Wi lliam son - 1

467027 Mercury

(Hg) 0.09 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Molybdenum(Mo) 5.83 mi lligramper kilogram (dry) (mg/kg)

FALSE 56 Wi lliam son - 1

467027 Nickel (Ni) 10.6 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Selenium(Se) 3.08 mi lligramper kilogram (dry) (mg/kg) FALSE 56 Wi lliam son - 1

467027 Vanadium(V) 37.7 mi lligramper kilogram (dry) (mg/kg) FALSE

Page 69test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 56 2005 PM Test - 2

compliance Annual filterable particulate emissions test. Report submitted to the Alabama Department of Environmental Management 6/22/2005 6/22/2005 No No 56 2005 PM Test - 3

compliance Annual filterable particulate emissions test. Report submitted to the Alabama Department of Environmental Management 6/22/2005 6/22/2005 No No 56 2005 PM Test -1

compliance Annual filterable particulate emissions testing. Report submitted to the Alabama Department of Environmental Management. 6/22/2005 6/22/2005 No No 56 2006 PM Test - 1

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/20/2006 6/20/2006 No No 56 2006 PM Test - 2

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/21/2006 6/21/2006 No No 56 2006 PM Test - 3

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/21/2006 6/21/2006 No No 56 2007 PM Test - 1

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management 6/19/2007 6/19/2007 No No 56 2007 PM Test - 2

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/20/2007 6/20/2007 No No 56 2007 PM Test - 3

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/20/2007 6/20/2007 No No 56 2008 PM Test - 1

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 7/29/2008 7/29/2008 No No 56 2008 PM test - 2

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/17/2008 6/17/2008 No No 56 2008 PM Test - 3

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 6/30/2008 6/30/2008 No No 56 2009 PM Test - 1

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 7/21/2009 7/21/2009 No No 56 2009 PM Test - 2

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. ######## ######## No No 56 2009 PM Test - 3

compliance Annual filterable particulate test. Report submitted to the Alabama Department of Environmental Management. 7/22/2009 7/22/2009 No No 56 Annual Com pliance Certification Report

compliance Provides compliance status of each unit for the past year with each proviso of the Title V Permit. Also provides methods by which compliance was determined. Report provided to the Alabama Department of Environmental Management and EPA Region 4. No No 56 Combustion Tuning and Mercury Measurement other Investigative This test evaluated the effects of unit boiler combustion tuning on NOx and Hg emissions, simultaneously. This data was also correlated with LOI on a real-time basis. (See further explanation in "Notes" screen.)

3/26/2005 4/2/2005 Yes No

Page 70test_reports

deviation_reports No No No No No No No No No No No No No No No Yes No

Page 71test_report_configurations

facility _id report_id configuration_id 56 2005 PM Test - 2

2 56 2005 PM Test - 3

3 56 2005 PM Test -1

1B 56 2006 PM Test - 1

1 56 2006 PM Test - 2

2 56 2006 PM Test - 3

3 56 2007 PM Test - 1

1B 56 2007 PM Test - 2

2 56 2007 PM Test - 3

3 56 2008 PM Test - 1

1B 56 2008 PM test - 2

2 56 2008 PM Test - 3

2 56 2009 PM Test - 1

1B 56 2009 PM Test - 2

2 56 2009 PM Test - 3

3C 56 2009 PM Test - 3

3D 56 Annual Com pliance Certification Report

1 56 Annual Com pliance Certification Report

2 56 Annual Com pliance Certification Report

3C 56 Annual Com pliance Certification Report

3D 56 Combustion Tuning and Mercury Measurement 1B

Page 72test_report_fuels

facility _id report_id fuel_id 56 2005 PM Test - 2

Bitum inous coal 56 2005 PM Test - 3

Bitum inous coal 56 2005 PM Test -1

Bium inous coal 56 2006 PM Test - 1

Bitum inous coal 56 2006 PM Test - 2

Bitum inous coal 56 2006 PM Test - 3

Bitum inous coal 56 2007 PM Test - 1

Bitum inous coal 56 2007 PM Test - 2

Bitum inous coal 56 2007 PM Test - 3

Bitum inous coal 56 2008 PM Test - 1

Bitum inous coal 56 2008 PM test - 2

Bitum inous coal 56 2008 PM Test - 3

Bitum inous coal 56 2009 PM Test - 1

Bitum inous coal 56 2009 PM Test - 2

Bitum inous coal 56 2009 PM Test - 3

Bitum inous coal 56 Annual Com pliance Certification Report

Bitum inous coal 56 Combustion Tuning and Mercury Measurement Bitum inous coal

Page 73test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 56 2005 PM Test - 2

Bitum inous coal

coal - bituminous 100 100 56 2005 PM Test - 3

Bitum inous coal

coal - bituminous 100 100 56 2005 PM Test -1

Bium inous coal

coal - bituminous 100 100 56 2006 PM Test - 1

Bitum inous coal

coal - bituminous 100 100 56 2006 PM Test - 2

Bitum inous coal

coal - bituminous 100 100 56 2006 PM Test - 3

Bitum inous coal

coal - bituminous 100 100 56 2007 PM Test - 1

Bitum inous coal

coal - bituminous 100 100 56 2007 PM Test - 2

Bitum inous coal

coal - bituminous 100 100 56 2007 PM Test - 3

Bitum inous coal

coal - bituminous 100 100 56 2008 PM Test - 1

Bitum inous coal

coal - bituminous 100 100 56 2008 PM test - 2

Bitum inous coal

coal - bituminous 100 100 56 2008 PM Test - 3

Bitum inous coal

coal - bituminous 100 100 56 2009 PM Test - 1

Bitum inous coal

coal - bituminous 100 100 56 2009 PM Test - 2

Bitum inous coal

coal - bituminous 100 100 56 2009 PM Test - 3

Bitum inous coal

coal - bituminous 100 100 56 Annual Com pliance Certification Report

Bitum inous coal

coal - bituminous 100 100 56 Combustion Tuning and Mercury Measurement Bitum inous coal

coal - bituminous 100 100

Page 74cem_data

facility _id tim e_period

cem_period_description 56 Hourly

and minute data NOx, SO2 and CO2 emissions data are available on an hourly and minute basis for each test run. 56 Mid-1990s to present

Hourly and minute NOx, SO2, CO2 and Opacity emissions data available for all units operating times and during the combustion tuning test.

Page 75cem_data

NOx, SO2 and CO2 emissions data are available on an hourly and minute basis for each test run. Hourly and minute NOx, SO2, CO2 and Opacity emissions data available for all units operating times and during the combustion tuning test.

Page 76cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 56 Mid-1990s to present

Nitrogen Oxide (NOx) 56 Mid-1990s to present

Sulfur Dioxide (SO2) 56 Mid-1990s to present

PM (Filterable) 56 Hourly

and minute data Nitrogen Oxide (NOx) 56 Hourly

and minute data PM (Filterable) 56 Hourly

and minute data Sulfur Dioxide (SO2)

Page 77test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 56 2005 PM Test - 2

MS03C No 56 2005 PM Test - 3

MS0D No No 56 2005 PM Test -1

MS001 Yes Sam pling ports are located in a rectangular duct just upstream of the stack. No 56 2006 PM Test - 1

MS001 Yes The sampling ports are located in a rectangular duct just upstream of the stack. No 56 2006 PM Test - 2

MS03C No 56 2006 PM Test - 3

MS0D No 56 2007 PM Test - 1

MS001 Yes Test prots are located in a rectangular duct just upstream of the stack. No 56 2007 PM Test - 2

MS03C No 56 2007 PM Test - 3

MS0D No 56 2008 PM Test - 1

MS001 Yes Sam pling ports are located in a rectangular duct just upstream of the stack. No 56 2008 PM test - 2

CS004 No 56 2008 PM Test - 3

MS0D No 56 2009 PM Test - 1

MS001 Yes The sampling ports are located within a rectangular duct just upstream of the stack. No 56 2009 PM Test - 2

CS004 No 56 2009 PM Test - 3

MS0D No 56 Annual Com pliance Certification Report

CS004 This is a compliance report only. It does not include any sampling or test results. "CS004" entry above is a placeholder only to satisfy

the software operation. 56 Combustion Tuning and Mercury Measurement MS001 Yes The sampling ports on this stack are located within a rectangular ductwork just upstream of the stack. (Please see explanation in "Notes" Screen.) No

Page 78test_report_sampling

fg_fraction 100% 100% 100% 100% 100% 100% 100% 100% 100% 100% 100% 100% 100% 100% 100% This is a compliance report only. It does not include any sampling or test results. "CS004" entry above is a placeholder only to satisfy

the software operation. 100%

Page 79sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 56 2005 PM Test - 2

MS03C average 6/23/2005 6/23/2005 245 9.1 56 2005 PM Test - 3

MS0D average 6/23/2005 6/23/2005 245 7.4 56 2005 PM Test -1

MS001 average 3/22/2005 6/22/2005 82 7.1 56 2006 PM Test - 1

MS001 average 6/20/2006 6/20/2006 82 9.9 56 2006 PM Test - 2

MS03C average 6/21/2006 6/21/2006 245 13.8 56 2006 PM Test - 3

MS0D average 6/21/2006 6/21/2006 245 10.6 56 2007 PM Test - 1

MS001 average 6/19/2007 6/19/2007 82 9.1 56 2007 PM Test - 2

MS03C average 6/20/2007 6/20/2007 245 14.4 56 2007 PM Test - 3

MS0D average 6/20/2007 6/20/2007 245 12.2 56 2008 PM Test - 1

MS001 average 7/29/2008 7/29/2008 82 8.7 56 2008 PM test - 2

CS004 average 6/17/2008 6/17/2008 245 14.9 56 2008 PM Test - 3

MS0D average 6/30/2008 6/30/2008 245 14.8 56 2009 PM Test - 1

MS001 average 7/21/2009 7/21/2009 82 8.5 56 2009 PM Test - 2

CS004 average ######## ######## 245 15.7 56 2009 PM Test - 3

MS0D average 7/22/2009 7/22/2009 245 13.5 56 Combustion Tuning and Mercury Measurement MS001 1

Page 80sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 633769 dscfm 98 30.1 6.37 11.67 165 627145 dscfm 87 30.15 6.2 12 190 240858 dscfm 88 30.2 8.03 10 270 244243 dscfm 92 30.05 7.5 10 266 651202 dscfm 96 30 5.8 10.8 199 314898 dscfm 90 30.15 7.3 11.3 202 240411 dscfm 83 29.7 8 10.5 251 626590 dscfm 86 29.7 7.8 11.3 189 582816 dscfm 79 29.95 7.2 11 191 262073 dscfm 90 30.5 8.3 11 259 609249 dscfm 96 29.8 7.7 12.2 130 618722 dscfm 89 30.2 7.6 12.6 134 253616 dscfm 82 29.62 7.8 11 259 593364 dscfm 83 30 7.8 11.8 132 323104 dscfm 81 29.98 7 11.8 127

Page 81sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 0.75 EPA Method 5 0.65 EPA Method 5 1.5 EPA Method 17 1.5 EPA Method 17 0.75 EPA Method 5 0.65 EPA Method 5 1.5 EPA Method 17 0.75 EPA Method 5 0.75 EPA Method 5 1.5 EPA Method 17 0.8 EPA Method 5 0.3 EPA Method 5 1.3 EPA Method 17 0.6 EPA Method 5 0.4 EPA Method 5 Please see explanantion given on the "Notes" screen for no test results being included with this submission for this test.

Page 82sampling_runs

fuel_sulfur

Please see explanantion given on the "Notes" screen for no test results being included with this submission for this test.

Page 83sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 56 2005 PM Test -1

MS001 average PM (Filterable) 0.0042 FALSE 56 2005 PM Test - 2

MS03C average PM (Filterable) 0.0127 FALSE 56 2005 PM Test - 3

MS0D average PM (Filterable) 0.0151 FALSE 56 2006 PM Test - 1

MS001 average PM (Filterable) 0.0081 FALSE 56 2006 PM Test - 2

MS03C average PM (Filterable) 0.0137 FALSE 56 2006 PM Test - 3

MS0D average PM (Filterable) 0.015 FALSE 56 2007 PM Test - 1

MS001 average PM (Filterable) 0.028 FALSE 56 2007 PM Test - 2

MS03C average PM (Filterable) 0.013 FALSE 56 2007 PM Test - 3

MS0D average PM (Filterable) 0.005 FALSE 56 2008 PM Test - 1

MS001 average PM (Filterable) 0.0024 FALSE 56 2008 PM test - 2

CS004 average PM (Filterable) 0.011 FALSE 56 2008 PM Test - 3

MS0D average PM (Filterable) 0.016 FALSE 56 2009 PM Test - 1

MS001 average PM (Filterable) 0.003 FALSE 56 2009 PM Test - 2

CS004 average PM (Filterable) 0.006 FALSE 56 2009 PM Test - 3

MS0D average PM (Filterable) 0.009 FALSE

Page 84sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 8.7 pound per hour (lb/hr)

FALSE 0.0103 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 69 pound per hour (lb/hr)

FALSE 0.0286 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 80.9 pound per hour (lb/hr)

FALSE 0.034 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 17.1 pound per hour (lb/hr)

FALSE 0.0201 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 76.6 pound per hour (lb/hr)

FALSE 0.031 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 40.6 pound per hour (lb/hr)

FALSE 0.0167 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 58.7 pound per hour (lb/hr)

FALSE 0.066 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 68 pound per hour (lb/hr)

FALSE 0.029 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 35 pound per hour (lb/hr)

FALSE 0.0145 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 5.4 pound per hour (lb/hr)

FALSE 0.0064 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 76.3 pound per hour (lb/hr)

FALSE 0.033 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 86.1 pound per hour (lb/hr)

FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 6.2 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 32.5 pound per hour (lb/hr)

FALSE 0.014 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen 51.4 pound per hour (lb/hr)

FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE See Notes Screen

Page 85sampling_run_pollutants1

run_pollutant_comment See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen See Notes Screen

Page 86sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 87sampling_run_fuel

fuel_conc_MDL

Page 88