# APPENDIX D. ANNUAL ENERGY SIMULATION INPUTS AND RESULTS FOR

COMMERCIAL REFRIGERATION EQUIPMENT

TABLE OF CONTENTS

**D.1 INTRODUCTION...........................................................................................................D­1** 

**D.2 MODELED**  **DESIGN OPTIONS AND**  **EFFICIENCY LEVELS ..................................D­2** 

**D.3 TABLES**  **OF ANNUAL**  **ENERGY SIMULATION RESULTS**  **AND**

**ENGINEERING ANALYSIS .......................................................................................D­10** 

**D.5 DAILY**  **ENERGY CONSUMPTION FOR**  **BASELINE EFFICIENCY**  **FOR FIVE** 

**CLIMATE LOCATIONS**  **.............................................................................................D­21**

**D.6 COMPARISON OF**  **DAILY ENERGY**  **CONSUMPTION BETWEEN**

**SIMULATION RESULTS AND**  **ENGINEERING ANALYSIS .................................D­24** 

**D.7 COMPARISON OF**  **DAILY ENERGY**  **SAVINGS BETWEEN SIMULATION** 

**RESULTS AND**  **ENGINEERING ANALYSIS ...........................................................D­36** 

**D.8 COMPARISON OF**  **ENERGY SAVINGS**  **BETWEEN REFRIGERATION**

**SYSTEM AND**  **WHOLE BUILDING..........................................................................D­39** 

LIST OF FIGURES

**Figure D.3.1**  **Case Refrigeration**  **Load for**  **VOP.RC.M............................................................D­18**

**Figure D.3.2**  **Case Refrigeration**  **Load for**  **SVO.RC.M............................................................D­18**

**Figure D.3.3**  **Case Refrigeration**  **Load for**  **VCT.RC.M............................................................D­18**

**Figure D.3.4**  **Case Refrigeration**  **Load for**  **HZO.RC.M ...........................................................D­19** 

**Figure D.3.5**  **Case Refrigeration**  **Load for**  **SOC.RC.M............................................................D­19**

**Figure D.3.6**  **Case Refrigeration**  **Load for**  **VOP.RC.L.............................................................D­19**

**Figure D.3.7**  **Case Refrigeration**  **Load for**  **VCT.RC.L.............................................................D­20**

**Figure D.5.1**  **Daily Energy**  **Consumption for**  **Baseline Efficiency**  **for VOP.RC.M.................D­21** 

**Figure D.5.2**  **Daily Energy**  **Consumption for**  **Baseline Efficiency**  **for SVO.RC.M.................D­21** 

**Figure D.5.3**  **Daily Energy**  **Consumption for**  **Baseline Efficiency**  **for VCT.RC.M.................D­21** 

**Figure D.5.4**  **Daily Energy**  **Consumption for**  **Baseline Efficiency**  **for HZO.RC.M.................D­22** 

**Figure D.5.5 Daily Energy Consumption for Baseline Efficiency for SOC.RC.M .................D­22** 

**Figure D.5.6**  **Daily Energy**  **Consumption for**  **Baseline Efficiency**  **for VOP.RC.L..................D­22** 

**Figure D.5.7**  **Daily Energy**  **Consumption for**  **Baseline Efficiency**  **for VCT.RC.L..................D­23** 

**Figure D.6.1**  **Daily Energy**  **Consumption for**  **VOP.RC.M for**  **Baltimore ................................D­24** 

**Figure D.6.2**  **Daily Energy**  **Consumption for**  **VOP.RC.M for**  **Chicago...................................D­24**

**Figure D.6.3**  **Daily Energy**  **Consumption for**  **VOP.RC.M for**  **Houston...................................D­24**

**Figure D.6.4 Daily Energy Consumption for VOP.RC.M for Los Angeles ............................D­25** 

**Figure D.6.5 Daily Energy Consumption for VOP.RC.M for Memphis .................................D­25** 

**Figure D.6.6**  **Daily Energy**  **Consumption for**  **SVO.RC.M for**  **Baltimore ................................D­25** 

**Figure D.6.7 Daily Energy Consumption for SVO.RC.M for Chicago ...................................D­26** 

**Figure D.6.8**  **Daily Energy**  **Consumption for**  **SVO.RC.M for**  **Houston...................................D­26**

**Figure D.6.9 Daily Energy Consumption for SVO.RC.M for Los Angeles ............................D­26** 

**Figure D.6.10 Daily Energy Consumption for SVO.RC.M for Memphis ...............................D­27** 

**Figure D.6.11**  **Daily Energy**  **Consumption for**  **VCT.RC.M for**  **Baltimore ..............................D­27** 

**Figure D.6.12**  **Daily Energy**  **Consumption for**  **VCT.RC.M for**  **Chicago.................................D­27**

**D­i**

# Figure **D.6.13 Daily**  **Energy Consumption**  **for VCT.RC.M**  **for Houston.................................D­28** 

**Figure D.6.14 Daily Energy Consumption for VCT.RC.M for Los Angeles ..........................D­28** 

**Figure D.6.15 Daily Energy Consumption for VCT.RC.M for Memphis ...............................D­28** 

**Figure D.6.16 Daily Energy Consumption for HZO.RC.M for Baltimore ..............................D­29** 

**Figure D.6.17**  **Daily Energy**  **Consumption for**  **HZO.RC.M for**  **Chicago.................................D­29**

**Figure D.6.18**  **Daily Energy**  **Consumption for**  **HZO.RC.M for**  **Houston.................................D­29**

**Figure D.6.19**  **Daily Energy**  **Consumption for**  **HZO.RC.M for**  **Los Angeles..........................D­30** 

**Figure D.6.20**  **Daily Energy**  **Consumption for**  **HZO.RC.M for**  **Memphis...............................D­30**

**Figure D.6.21**  **Daily Energy**  **Consumption for**  **SOC.RC.M for**  **Baltimore ..............................D­30** 

**Figure D.6.22 Daily Energy Consumption for SOC.RC.M for Chicago .................................D­31** 

**Figure D.6.23**  **Daily Energy**  **Consumption for**  **SOC.RC.M for**  **Houston.................................D­31**

**Figure D.6.24**  **Daily Energy**  **Consumption for**  **SOC.RC.M for**  **Los Angeles**  **..........................D­31**

**Figure D.6.25**  **Daily Energy**  **Consumption for**  **SOC.RC.M for**  **Memphis ...............................D­32** 

**Figure D.6.26**  **Daily Energy**  **Consumption for**  **VOP.RC.L for**  **Baltimore ...............................D­32** 

**Figure D.6.27 Daily Energy Consumption for VOP.RC.L for Chicago ..................................D­32** 

**Figure D.6.28**  **Daily Energy**  **Consumption for**  **VOP.RC.L for**  **Houston..................................D­33**

**Figure D.6.29**  **Daily Energy**  **Consumption for**  **VOP.RC.L for**  **Los Angeles**  **...........................D­33**

**Figure D.6.30**  **Daily Energy**  **Consumption for**  **VOP.RC.L for**  **Memphis ................................D­33** 

**Figure D.6.31**  **Daily Energy**  **Consumption for**  **VCT.RC.L for**  **Baltimore ...............................D­34** 

**Figure D.6.32 Daily Energy Consumption for VCT.RC.L for Chicago ..................................D­34** 

**Figure D.6.33**  **Daily Energy**  **Consumption for**  **VCT.RC.L for**  **Houston..................................D­34**

**Figure D.6.34**  **Daily Energy**  **Consumption for**  **VCT.RC.L for**  **Los Angeles**  **...........................D­35**

**Figure D.6.35**  **Daily Energy**  **Consumption for**  **VCT.RC.L for**  **Memphis ................................D­35** 

**Figure D.7.1**  **Daily Energy**  **Savings for**  **VOP.RC.M................................................................D­36**

**Figure D.7.2**  **Daily Energy**  **Savings for**  **SVO.RC.M................................................................D­36**

**Figure D.7.3**  **Daily Energy**  **Savings for**  **VCT.RC.M................................................................D­36**

**Figure D.7.4**  **Daily Energy**  **Savings for**  **HZO.RC.M................................................................D­37**

**Figure D.7.5 Daily Energy Savings for SOC.RC.M ................................................................D­37** 

**Figure D.7.6**  **Daily Energy**  **Savings for**  **VOP.RC.L.................................................................D­37**

**Figure D.7.7**  **Daily Energy**  **Savings for**  **VCT.RC.L.................................................................D­38**

**Figure D.8.1**  **Daily Energy**  **Savings for**  **Baltimore (Refrigeration**  **System versus**  **Whole**

**Building) ..........................................................................................................D­39** 

**Figure D.8.2**  **Daily Energy**  **Savings for**  **Chicago (Refrigeration**  **System versus** 

**Whole Building)**  **..............................................................................................D­39**

**Figure D.8.3**  **Daily Energy**  **Savings for**  **Houston (Refrigeration**  **System versus** 

**Whole Building)**  **..............................................................................................D­39**

**Figure D.8.4**  **Daily Energy**  **Savings for**  **Los Angeles**  **(Refrigeration System**  **versus**

**Whole Building)**  **..............................................................................................D­40**

**Figure D.8.5**  **Daily Energy**  **Savings for**  **Memphis (Refrigeration**  **System versus** 

**Whole Building)**  **..............................................................................................D­40**

**D­ii**

# APPENDIX D. ANNUAL ENERGY SIMULATION INPUTS AND RESULTS

FOR COMMERCIAL REFRIGERATION EQUIPMENT

D.1 INTRODUCTION

**This appendix**  **presents further**  **details on**  **annual energy**  **simulation inputs**  **and results** 

**discussed in**  **chapter 7,**  **Energy Use**  **and End­Use**  **Load Characterization.**  **Section D.2**  **shows**

**tables of**  **assumptions and**  **inputs used**  **in annual**  **energy simulation.**  **Sections D.3**  **through D.7** 

**present tables**  **and figures**  **of the**  **simulations results**  **for the**  **commercial refrigeration**  **equipment**

**analyzed; this**  **includes comparisons**  **of CRE**  **refrigeration load**  **and daily**  **energy consumption** 

**between the**  **simulation results**  **and the**  **engineering analysis.**  **Section D.8**  **summarizes the**  **impact**

**of different**  **refrigeration system**  **design options**  **on whole**  **building energy**  **use.**

**D­1**

# D.2 MODELED DESIGN OPTIONS AND EFFICIENCY LEVELS

Table D.2.1 Summary of Modeled Design Options for VOP.RC.M

**Equipment Class**  **VOP.RC.M**

**Efficiency Level**  **AD1 AD3**  **AD5 AD6** 

**Equipment Temperature**  **(°F) 38.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) 32.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) 15.0**  **15.0 21.8**  **21.8**

**Total Refrigeration**  **Load (Btu/hr)**  **20,587.0 19,945.0**  **19,784.0 18,964.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **16,050.0 16,050.0**  **16,050.0 16,050.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 1,458.0**  **1,458.0 1,458.0**  **1,458.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **6**

**Power Consumption** 

**per Fan**  **(W) 45.0**  **13.6 13.6**  **13.6**

**Fan Operating**  **Hrs 24.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 15** 

**No. of**  **Bulbs Outside** 

**Case 12** 

**Power Consumption** 

**per Bulb**  **(W) 30.1**  **30.1 27.8**  **16.4**

**No. of**  **Ballasts Inside** 

**Case 0** 

**No. of**  **Ballasts Outside** 

**Case 9** 

**Power Consumption** 

**per Ballast**  **(W) 1.4**  **1.4 1.7**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Off­time** 

**Total Defrost**  **Time per** 

**Day (hrs)**  **4.5**

**Defrost Heater**  **Power**

**(W) 0.0** 

**Anti­Sweat**

**Heater Other**  **Power (W)**  **0.0**

**Door Power**  **(W) 0.0** 

**Other Run**  **Time per** 

**Day (hrs)**  **0.0**

**Door Run**  **Time per** 

**Day (hrs)**  **0.0**

**D­2**

# Table D.2.2 Summary of Modeled Design Options for SVO.RC.M

**Equipment Class**  **SVO.RC.M**

**Efficiency Level**  **AD1 AD3**  **AD5 AD6** 

**Equipment Temperature**  **(°F) 38.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) 32.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) 15.0**  **15.0 21.8**  **21.8**

**Total Refrigeration**  **Load (Btu/hr)**  **14,520.0 14,091.0**  **13,988.0 13,461.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **10,981.0 10,981.0**  **10,981.0 10,981.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 1,250.0**  **1,250.0 1,250.0**  **1,250.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **4**

**Power Consumption** 

**per Fan**  **(W) 45.0**  **13.6 13.6**  **13.6**

**Fan Operating**  **Hrs 24.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 9** 

**No. of**  **Bulbs Outside** 

**Case 9** 

**Power Consumption** 

**per Bulb**  **(W) 30.1**  **30.1 27.8**  **16.4**

**No. of**  **Ballasts**

**Inside Case**  **0**

**No. of**  **Ballasts**

**Outside Case**  **6**

**Power Consumption** 

**per Ballast**  **(W) 1.4**  **1.4 1.7**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Off­time** 

**Total Defrost**  **Time**

**per Day**  **(hrs) 3.0** 

**Defrost Heater** 

**Power (W)**  **0.0**

**Anti­Sweat**

**Heater Other**  **Power (W)**  **120.0**

**Door Power**  **(W) 0.0** 

**Other Run**  **Time per** 

**Day (hrs)**  **24.0**

**Door Run**  **Time per** 

**Day (hrs)**  **0.0**

**D­3**

# Table D.2.3 Summary of Modeled Design Options for VCT.RC.M

**Equipment Class**  **VCT.RC.M**

**Efficiency Level**  **AD1 AD4**  **AD6 AD7** 

**Equipment Temperature**  **(°F) 38.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) 35.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) 15.0**  **15.0 23.0**  **23.0**

**Total Refrigeration**  **Load (Btu/hr)**  **5,383.0 4,333.0**  **3,403.0 3,054.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **209.0 209.0**  **209.0 209.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 2,062.0**  **2,062.0 1,849.0**  **1,849.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **5**

**Power Consumption** 

**per Fan**  **(W) 30.0**  **9.1 9.1**  **9.1**

**Fan Operating**  **Hrs 24.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 6** 

**No. of**  **Bulbs Outside** 

**Case 0** 

**Power Consumption** 

**per Bulb**  **(W) 77.4**  **58.0 58.0**  **41.0**

**No. of**  **Ballasts**

**Inside Case**  **6**

**No. of**  **Ballasts**

**Outside Case**  **0**

**Power Consumption** 

**per Ballast**  **(W) 14.5**  **0.0 0.0**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Off­time** 

**Total Defrost**  **Time**

**per Day**  **(hrs) 1.0** 

**Defrost Heater** 

**Power (W)**  **0**

**Anti­Sweat**

**Heater Other**  **Power (W)**  **0.0**

**Door Power**  **(W) 300.0**  **300.0 0.0**  **0.0**

**Other Run**  **Time per** 

**Day (hrs)**  **0.0**

**Door Run**  **Time per** 

**Day (hrs)**  **24.0 24.0**  **0.0 0.0** 

**D­4**

# Table D.2.4 Summary of Modeled Design Options for HZO.RC.M

**Equipment Class**  **HZO.RC.M**

**Efficiency Level**  **AD1 AD2**  **AD3 AD5** 

**Equipment Temperature**  **(°F) 38.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) 32.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) 15.0**  **15.0 15.0**  **21.8**

**Total Refrigeration**  **Load (Btu/hr)**  **2,365.0 2,238.0**  **2,080.0 2,080.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **619.0 619.0**  **619.0 619.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 1,336.0**  **1,336.0 1,336.0**  **1,336.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **4**

**Power Consumption** 

**per Fan**  **(W) 30.0**  **20.7 9.1**  **9.1**

**Fan Operating**  **Hrs 24.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 0** 

**No. of**  **Bulbs Outside** 

**Case 0** 

**Power Consumption** 

**per Bulb**  **(W) 0.0**  **0.0 0.0**  **0.0**

**No. of**  **Ballasts**

**Inside Case**  **0**

**No. of**  **Ballasts**

**Outside Case**  **0**

**Power Consumption** 

**per Ballast**  **(W) 0.0**  **0.0 0.0**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Off­time** 

**Total Defrost**  **Time**

**per Day**  **(hrs) 2.0** 

**Defrost Heater** 

**Power (W)**  **0.0**

**Anti­Sweat**

**Heater Other**  **Power (W)**  **0.0**

**Door Power**  **(W) 0.0** 

**Other Run**  **Time per** 

**Day (hrs)**  **0.0**

**Door Run**  **Time per** 

**Day (hrs)**  **0.0**

**D­5**

# Table D.2.5 Summary of Modeled Design Options for SOC.RC.M

**Equipment Class**  **SOC.RC.M**

**Efficiency Level**  **AD1 AD3**  **AD4 AD7** 

**Equipment Temperature**  **(°F) 38.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) 35.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) 15.0**  **15.0 15.0**  **21.0**

**Total Refrigeration**  **Load (Btu/hr)**  **7,069.0 5,944.0**  **5,829.0 4,959.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **279.0 279.0**  **279.0 279.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 2,181.0**  **2,181.0 2,181.0**  **1,896.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **12**

**Power Consumption** 

**per Fan**  **(W) 45.0**  **13.6 13.6**  **13.6**

**Fan Operating**  **Hrs 21.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 15** 

**No. of**  **Bulbs Outside** 

**Case 0** 

**Power Consumption** 

**per Bulb**  **(W) 30.1**  **30.1 27.8**  **16.4**

**No. of**  **Ballasts**

**Inside Case**  **0**

**No. of**  **Ballasts**

**Outside Case**  **5**

**Power Consumption** 

**per Ballast**  **(W) 1.4**  **1.4 1.7**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Electric** 

**Total Defrost**  **Time**

**per Day**  **(hrs) 3.0** 

**Defrost Heater** 

**Power (W)**  **1200.0**

**Anti­Sweat**

**Heater Other**  **Power (W)**  **400.0**

**Door Power**  **(W) 0.0** 

**Other Run**  **Time per** 

**Day (hrs)**  **24.0**

**Door Run**  **Time per** 

**Day (hrs)**  **0.0**

**D­6**

# Table D.2.6 Summary of Modeled Design Options for VOP.RC.L

**Equipment Class**  **VOP.RC.L**

**Efficiency Level**  **AD1 AD3**  **AD5 AD6** 

**Equipment Temperature**  **(°F) 0.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) ­5.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) ­20.0**  **­20.0 ­14.0**  **­14.0**

**Total Refrigeration**  **Load (Btu/hr)**  **23,575.0 22,200.0**  **22,166.0 12,990.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **15,277.0 15,277.0**  **15,277.0 15,277.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 2,567.0**  **2,567.0 2,567.0**  **2,567.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **14**

**Power Consumption** 

**per Fan**  **(W) 45.0**  **13.6 13.6**  **13.6**

**Fan Operating**  **Hrs 22.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 0** 

**No. of**  **Bulbs Outside** 

**Case 9** 

**Power Consumption** 

**per Bulb**  **(W) 30.1**  **30.1 27.8**  **16.4**

**No. of**  **Ballasts**

**Inside Case**  **0**

**No. of**  **Ballasts**

**Outside Case**  **3**

**Power Consumption** 

**per Ballast**  **(W) 1.4**  **1.4 1.7**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Electric** 

**Total Defrost**  **Time**

**per Day**  **(hrs) 2.0** 

**Defrost Heater** 

**Power (W)**  **8,700.0**

**Anti­Sweat**

**Heater Other**  **Power (W)**  **600.0**

**Door Power**  **(W) 0.0** 

**Other Run**  **Time per** 

**Day (hrs)**  **24.0**

**Door Run**  **Time per** 

**Day (hrs)**  **0.0**

**D­7**

# Table D.2.7 Summary of Modeled Design Options for VCT.RC.L

**Equipment Class**  **VCT.RC.L**

**Efficiency Level**  **AD1 AD4**  **AD6 AD7** 

**Equipment Temperature**  **(°F) 0.0** 

**Discharge Air**  **Temperature (DAT)**  **(°F) ­3.0** 

**Saturated Evaporator**  **Temperature (SET)**  **(°F) ­11.0**  **­11.0 ­7.8**  **­7.8**

**Total Refrigeration**  **Load (Btu/hr)**  **9,593.0 8,558.0**  **5,964.0 5,616.0** 

**Non**

**Electric**

**Load Infiltration**  **Load (Btu/hr)**  **887.0 887.0**  **887.0 887.0** 

**Conduction and**  **Radiation Load** 

**(Btu/hr) 3,746.0**  **3,746.0 2,347.0**  **2,347.0**

**Electric**

**Load Evaporator** 

**Fan No.**  **of Fans**  **5**

**Power Consumption** 

**per Fan**  **(W) 30.0**  **9.1 9.1**  **9.1**

**Fan Operating**  **Hrs 23.0** 

**Lighting No.**  **of Bulbs**  **Inside**

**Case 6** 

**No. of**  **Bulbs Outside** 

**Case 0** 

**Power Consumption** 

**per Bulb**  **(W) 77.4**  **58.0 58.0**  **41.0**

**No. of**  **Ballasts**

**Inside Case**  **6**

**No. of**  **Ballasts**

**Outside Case**  **0**

**Power Consumption** 

**per Ballast**  **(W) 14.5**  **0.0 0.0**  **0.0**

**Defrost**

**Heater Defrost**  **Mechanism Electric** 

**Total Defrost**  **Time**

**per Day**  **(hrs) 1.0** 

**Defrost Heater** 

**Power (W)**  **5,000.0**

**Anti­Sweat**

**Heater Other**  **Power (W)**  **0.0**

**Door Power**  **(W) 800.0**  **800.0 300.0**  **300.0**

**Other Run**  **Time per** 

**Day (hrs)**  **0.0**

**Door Run**  **Time per** 

**Day (hrs)**  **24.0**

**D­8**TableD.2.8DOE­2.2RInputParameters forModeledDisplayCases



## D­9EquipmentClassEfficiencyLevelsSET(°F)TemperatureDifferencebetweenSETandDAT(°F)Infiltration(Btu/hr­ft)*Conduction&Radiation(Btu/hr­ft)*EvaporatorFan(kW/ft)*Lighting(kW/ft)*RatioofLightingLoadtoHVACZoneAntiSweat(kW/ft)***VOP.RC.M AD1** **15.0 17.0** **1,337.5 121.5** **0.0225 0.0688** **0.23 0** **AD3 15.0** **17.0 1,337.5** **121.5 0.0068** **0.0688 0.23** **0 AD5** **21.8 10.2** **1,337.5 121.5** **0.0068 0.0638** **0.24 0** **AD6 21.8** **10.2 1,337.5** **121.5 0.0068** **0.0369 0.22** **0 SVO.RC.M** **AD1 15.0** **17.0 915.1** **104.2 0.0150** **0.0459 0.26** **0.0100 AD3** **15.0 17.0** **915.1 104.2** **0.0045 0.0459** **0.26 0.0100** **AD5 21.8** **10.2 915.1** **104.2 0.0045** **0.0426 0.26** **0.0100 AD6** **21.8 10.2** **915.1 104.2** **0.0045 0.0246** **0.25 0.0100** **VCT.RC.M AD1** **15.0 20.0** **41.8 412.4** **0.0300 0.1103** **0 0.0600** **AD4 15.0** **20.0 41.8** **412.4 0.0091** **0.0696 0** **0.0600 AD6** **23.0 12.0** **41.8 369.8** **0.0091 0.0696** **0 0.0000** **AD7 23.0** **12.0 41.8** **369.8 0.0091** **0.0492 0** **0.0000 HZO.RC.M** **AD1 15.0** **17.0 51.6** **111.3 0.0100** **0 0** **0 AD2** **15.0 17.0** **51.6 111.3** **0.0069 0** **0 0** **AD3 15.0** **17.0 51.6** **111.3 0.0030** **0 0** **0 AD5** **21.8 10.2** **51.6 111.3** **0.0030 0** **0 0** **SOC.RC.M AD1** **15.0 20.0** **23.3 181.8** **0.0450 0.0382** **0.02 0.0333** **AD3 15.0** **20.0 23.3** **181.8 0.0136** **0.0382 0.02** **0.0333 AD4** **15.0 20.0** **23.3 181.8** **0.0136 0.0355** **0.02 0.0333** **AD7 21.0** **14.0 23.3** **158.0 0.0136** **0.0205 0.00** **0.0333 VOP.RC.L** **AD1 ­20.0** **15.0 1,273.1** **213.9 0.0525** **0.0229 0.51** **0.0500 AD3** **­20.0 15.0** **1,273.1 213.9** **0.0159 0.0229** **0.51 0.0500** **AD5 ­14.0** **9.0 1,273.1** **213.9 0.0159** **0.0213 0.51** **0.0500 AD6** **­14.0 9.0** **1,273.1 213.9** **0.0159 0.0123** **0.50 0.0500** **VCT.RC.L AD1** **­11.0 8.0** **177.4 749.2** **0.0300 0.1103** **0.00 0.1600** **AD4 ­11.0** **8.0 177.4** **749.2 0.0091** **0.0696 0.00** **0.1600 AD6** **­7.8 4.8** **177.4 469.4** **0.0091 0.0696** **0.00 0.0600** **AD7 ­7.8** **4.8 177.4** **469.4 0.0091** **0.0492 0.00** **0.0600*********For display** **cases with** **doors, unit** **is Btu/hr­door** **or kW/door.** D.3TABLESOFANNUALENERGYSIMULATIONRESULTSANDENGINEERINGANALYSISTableD.3.1ComparisonofAnnualEnergySimulationandEngineeringAnalysis forVOP.RC.M



## D­10EfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **14,344 26.29** **34.27 20,587** **26.28 35.78** **Chicago 13,959** **32.43 Houston** **16,013 42.65** **Los Angeles** **14,746 32.3** **Memphis 15,042** **38.6 AD3** **Baltimore 13,727** **21.77 32.83** **19,945 21.76** **34.66 Chicago** **13,340 30.86** **Houston 15,401** **41.06 Los** **Angeles 14,131** **31.05 Memphis** **14,424 37.09** **AD5 Baltimore** **13,487 20.33** **28.12 19,784** **20.36 30.74** **Chicago 13,108** **26.5 Houston** **15,091 35.2** **Los Angeles** **13,871 26.37** **Memphis 14,157** **31.79 AD6** **Baltimore 12,704** **12.59 26.45** **18,964 12.59** **29.47 Chicago** **12,322 24.73** **Houston 14,320** **33.44 Los** **Angeles 13,091** **24.95 Memphis** **13,379 30.07** TableD.3.2ComparisonofAnnualEnergySimulationandEngineeringAnalysis forSVO.RC.MEfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **10,302 20.42** **25.5 14,520** **20.4 27.18** **Chicago 10,024** **23.85 Houston** **11,512 31.72** **Los Angeles** **10,595 24.57** **Memphis 10,804** **28.59 AD3** **Baltimore 9,883** **17.39 24.46** **14,091 17.39** **26.37 Chicago** **9,605 22.83** **Houston 11,093** **30.63 Los** **Angeles 10,174** **23.53 Memphis** **10,385 27.52** **AD5 Baltimore** **9,755 16.44** **21.12 13,988** **16.46 23.41** **Chicago 9,485** **19.67 Houston** **10,918 26.45** **Los Angeles** **10,051 20.2** **Memphis 10,241** **23.79 AD6** **Baltimore 9,234** **11.26 19.98** **13,461 11.27** **22.52 Chicago** **8,961 18.56** **Houston 10,403** **25.24 Los** **Angeles 9,527** **19.1 Memphis** **9,723 22.61** 



## D­11TableD.3.3ComparisonofAnnualEnergySimulationandEngineeringAnalysis forVCT.RC.MEfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **5,068 24.04** **12.43 5,383** **24.02 11.03** **Chicago 5,057** **11.55 Houston** **5,126 13.68** **Los Angeles** **5,080 10.88** **Memphis 5,097** **13.05 AD4** **Baltimore 4,030** **16.64 9.84** **4,333 16.64** **8.88 Chicago** **4,013 9.63** **Houston 4,087** **10.91 Los** **Angeles 4,035** **9.12 Memphis** **4,058 10.39** **AD7 Baltimore** **3,128 9.44** **6.5 3,403** **9.44 6.09** **Chicago 3,116** **6.29 Houston** **3,185 7.25** **Los Angeles** **3,139 5.89** **Memphis 3,156** **6.86 AD7** **Baltimore 2,785** **7.00 5.78** **3,054 6.99** **5.47 Chicago** **2,774 5.66** **Houston 2,837** **6.47 Los** **Angeles 2,797** **5.35 Memphis** **2,814 6.11** 



## D­12TableD.3.4ComparisonofAnnualEnergySimulationandEngineeringAnalysis forHZO.RC.MEfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **2,003 2.88** **4.91 2,365** **2.88 4.64** **Chicago 1,981** **4.71 Houston** **2,089 5.65** **Los Angeles** **2,021 4.75** **Memphis 2,038** **5.29 AD2** **Baltimore 1,878** **1.99 4.61** **2,238 1.99** **4.39 Chicago** **1,855 4.41** **Houston 1,963** **5.32 Los** **Angeles 1,895** **4.47 Memphis** **1,918 4.98** **AD3 Baltimore** **1,724 0.86** **4.24 2,080** **0.87 4.08** **Chicago 1,701** **4.04 Houston** **1,815 4.92** **Los Angeles** **1,747 4.11** **Memphis 1,764** **4.6 AD5** **Baltimore 1,718** **0.86 3.69** **2,080 0.87** **3.65 Chicago** **1,695 3.51** **Houston 1,798** **4.3 Los** **Angeles 1,735** **3.58 Memphis** **1,752 4.01** 



## D­13TableD.3.5ComparisonofAnnualEnergySimulationandEngineeringAnalysis forSOC.RC.MEfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **6,821 35.53** **15.52 7,069** **35.54 13.23** **Chicago 6,787** **14.16 Houston** **6,861 16.84** **Los Angeles** **6,804 13.58** **Memphis 6,849** **16.35 AD3** **Baltimore 5,554** **27.62 12.52** **5,944 27.64** **11.13 Chicago** **5,531 11.9** **Houston 5,594** **13.78 Los** **Angeles 5,554** **11.4 Memphis** **5,576 13.18** **AD4 Baltimore** **5,445 26.84** **12.35 5,829** **26.86 10.97** **Chicago 5,422** **11.51 Houston** **5,491 13.57** **Los Angeles** **5,445 11** **Memphis 5,474** **12.97 AD7** **Baltimore 4,595** **22.52 9.14** **4,959 22.54** **8.1 Chicago** **4,578 8.82** **Houston 4,640** **10.09 Los** **Angeles 4,612** **8.42 Memphis** **4,618 9.65** 



## D­14TableD.3.6ComparisonofAnnualEnergySimulationandEngineeringAnalysis forVOP.RC.LEfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **19,977 52.27** **86.75 23,575** **52.26 78.56** **Chicago 19,732** **83.33 Houston** **20,999 97.78** **Los Angeles** **20,205 82.47** **Memphis 20,428** **92.85 AD3** **Baltimore 18,522** **42.61 80.38** **22,200 42.6** **74 Chicago** **18,271 77.11** **Houston 19,538** **90.96 Los** **Angeles 18,756** **76.62 Memphis** **18,973 86.29** **AD5 Baltimore** **18,430 42.14** **71.1 22,166** **42.13 67.82** **Chicago 18,156** **67.95 Houston** **19,481 81.03** **Los Angeles** **18,733 67.68** **Memphis 18,893** **76.6 AD6** **Baltimore 18,253** **39.55 70.4** **21,900 39.54** **67.28 Chicago** **17,974 67.3** **Houston 19,298** **80.25 Los** **Angeles 18,545** **67.04 Memphis** **18,699 75.54** 



## D­15TableD.3.7ComparisonofAnnualEnergySimulationandEngineeringAnalysis forVCT.RC.LEfficiencyLevelLocationAnnualSimulationResultsEngineeringAnalysisResultsCaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)CaseRefrigerationLoad(Btu/hr)CaseDailyDirectElectricUse(kWh/day)CompressorDailyEnergyUse(kWh/day)**AD1 Baltimore** **8,993 40.89** **31.94 9,593** **40.87 29.46** **Chicago 8,965** **30.63 Houston** **9,077 34.82** **Los Angeles** **8,990 29.66** **Memphis 9,038** **33.6 AD4** **Baltimore 7,940** **33.6 28.22** **8,558 33.6** **26.28 Chicago** **7,904 27.01** **Houston 8,013** **30.76 Los** **Angeles 7,935** **26.08 Memphis** **7,977 29.69** **AD6 Baltimore** **5,417 21.6** **18.12 5,964** **21.6 17.51** **Chicago 5,400** **17.31 Houston** **5,488 19.74** **Los Angeles** **5,425 16.45** **Memphis 5,454** **19.13 AD7** **Baltimore 5,066** **19.15 17.02** **5,616 19.15** **16.49 Chicago** **5,045 16.17** **Houston 5,135** **18.52 Los** **Angeles 5,071** **15.37 Memphis** **5,099 17.98** 



## D­16TableD.3.8ComparisonofDailyEnergySavings fromAnnualSimulationandfromEngineeringAnalysisEquipmentClassSymbolEfficiencyLevelAnnualSimulationResults(kWh/day)EngineeringAnalysisResults(kWh/day)BaltimoreChicagoHoustonLosAngelesMemphis**VOP.RC.M AD3** **5.96 6.09** **6.11 5.77** **6.03 5.63** **AD5 12.11** **11.89 13.41** **11.90 12.78** **10.96 AD6** **21.53 21.41** **22.92 21.06** **22.24 20.00** **SVO.RC.M AD3** **4.06 4.04** **4.12 4.06** **4.09 3.82** **AD5 8.35** **8.16 9.25** **8.34 8.77** **7.69 AD6** **14.67 14.45** **15.64 14.63** **15.13 13.78** **VCT.RC.M AD4** **9.98 9.31** **10.17 9.15** **10.05 9.53** **AD6 20.53** **19.86 21.02** **19.58 20.78** **19.52 AD7** **23.70 22.94** **24.26 22.57** **23.98 22.59** **HZO.RC.M AD2** **1.19 1.19** **1.22 1.17** **1.21 1.15** **AD3 2.69** **2.68 2.74** **2.65 2.71** **2.57 AD5** **3.24 3.21** **3.37 3.19** **3.30 3.00** **SOC.RC.M AD3** **10.92 10.17** **10.97 10.09** **11.08 10.01** **AD4 11.86** **11.34 11.96** **11.26 12.06** **11.00 AD7** **19.38 18.35** **19.76 18.16** **19.71 18.13** **VOP.RC.L AD3** **16.04 15.89** **16.48 15.52** **16.22 14.24** **AD5 25.78** **25.52 26.88** **24.92 26.39** **20.88 AD6** **29.07 28.76** **30.25 28.15** **30.04 24.01** **VCT.RC.L AD4** **11.00 10.90** **11.34 10.86** **11.19 10.45** **AD6 33.10** **32.61 34.37** **32.50 33.75** **31.22 AD7** **36.66 36.19** **38.04 36.02** **37.35 34.69** 



## D­17

# D.4 COMPARISON OF CASE REFRIGERATION LOAD BETWEEN SIMULATION

AND ENGINEERING ANALYSIS

VOP.RC.MCaseRefrigerationLoad(Btu/hr) 25000

20000

15000

10000

5000

0 Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.3.1 Case Refrigeration Load for VOP.RC.M

SVO.RC.M

0 4000 8000 12000 16000CaseRefrigerationLoad(Btu/hr)

Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.3.2 Case Refrigeration Load for SVO.RC.M

VCT.RC.M

0 1000 2000 3000 4000 5000 6000CaseRefrigerationLoad(Btu/hr)

Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7



# Figure D.3.3 Case Refrigeration Load for VCT.RC.M

**D­18**CaseRefrigerationLoad(Btu/hr) 

## HZO.RC.M

2500

2000

1500

1000

Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5 Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering 

### 500

0



# Figure D.3.4 Case Refrigeration Load for HZO.RC.M

SOC.RC.MCaseRefrigerationLoad(Btu/hr) 

### 8000

6000

4000

2000

0 Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering



### Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.3.5 Case Refrigeration Load for SOC.RC.M

VOP.RC.LCaseRefrigerationLoad(Btu/hr) 

### 25000

20000

15000

10000

5000

0 Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering



### Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.3.6 Case Refrigeration Load for VOP.RC.L

**D­19**

## VCT.RC.LCaseRefrigerationLoad(Btu/hr) 

### 12000

9000

6000

3000

0

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7 Annual Sim._Baltimore Annual Sim._Chicago

Annual Sim._Houston Annual Sim._Los Angeles

Annual Sim._Memphis Engineering



# Figure D.3.7 Case Refrigeration Load for VCT.RC.L

**D­20**

# D.5 DAILY ENERGY CONSUMPTION FOR BASELINE EFFICIENCY FOR FIVE

CLIMATE LOCATIONS

VOP.RC.M­Eff Level AD1

80EnergyConsumption(kWh/Day)

60

40

20

0

Baltimore Chicago Houston Los Angeles Memphis 

### CompElec

C a s e D i r E l e c



# Figure D.5.1 Daily Energy Consumption for Baseline Efficiency for VOP.RC.M

SVO.RC.M­Eff Level AD1

60EnergyConsumption(kWh/Day) 50

40

30

20

10

0

Baltimore Chicago Houston Los Angeles Memphis 

### CompElec

C a s e D i r E l e c



# Figure D.5.2 Daily Energy Consumption for Baseline Efficiency for SVO.RC.M

VCT.RC.M­Eff Level AD1

0 10 20 30 40 50EnergyConsumption(kWh/Day) 

### CompElec



### C a s e D i r E l e c

Baltimore Chicago Houston Los Angeles Memphis



# Figure D.5.3 Daily Energy Consumption for Baseline Efficiency for VCT.RC.M

**D­21**

## HZO.RC.M­Eff Level AD1

10EnergyConsumption(kWh/Day)

8

6

4

2

0



### Baltimore Chicago Houston Los Angeles Memphis 

### CompElec

C a s e D i r E l e c



# Figure D.5.4 Daily Energy Consumption for Baseline Efficiency for HZO.RC.M

SOC.RC.M­Eff Level AD1

0 10 20 30 40 50 60 70EnergyConsumption(kWh/Day) 

### CompElec

C a s e D i r E l e c

Baltimore Chicago Houston Los Angeles Memphis



# Figure D.5.5 Daily Energy Consumption for Baseline Efficiency for SOC.RC.M

VOP.RC.L­Eff Level AD1

0 20 40 60 80 100 120 140 160 180EnergyConsumption(kWh/Day) 

### CompElec

C a s e D i r E l e c

Baltimore Chicago Houston Los Angeles Memphis



# Figure D.5.6 Daily Energy Consumption for Baseline Efficiency for VOP.RC.L

**D­22**

## VCT.RC.L­Eff Level AD1

0 10 20 30 40 50 60 70 80 90 100EnergyConsumption(kWh/Day) 

### CompElec



### C a s e D i r E l e c

Baltimore Chicago Houston Los Angeles Memphis



# Figure D.5.7 Daily Energy Consumption for Baseline Efficiency for VCT.RC.L

**D­23**

# D.6 COMPARISON OF DAILY ENERGY CONSUMPTION BETWEEN

SIMULATION RESULTS AND ENGINEERING ANALYSIS

VOP.RC.M­Baltimore

0 10 20 30 40 50 60 70AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c



# Figure D.6.1 Daily Energy Consumption for VOP.RC.M for Baltimore

VOP.RC.M­Chicago

0 10 20 30 40 50 60 70AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c



# Figure D.6.2 Daily Energy Consumption for VOP.RC.M for Chicago

VOP.RC.M­Houston

0 10 20 30 40 50 60 70AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c



# Figure D.6.3 Daily Energy Consumption for VOP.RC.M for Houston

**D­24**

### VOP.RC.M­Los AngelesEnergyConsumption(kWh/Day) 70

60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.4 Daily Energy Consumption for VOP.RC.M for Los Angeles

VOP.RC.M­MemphisEnergyConsumption(kWh/Day) 70

60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.5 Daily Energy Consumption for VOP.RC.M for Memphis

SVO.RC.M­BaltimoreEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a s e D i r E l e c

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.6.6 Daily Energy Consumption for SVO.RC.M for Baltimore

**D­25**

### SVO.RC.M­ChicagoEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a s e D i r E l e c

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.6.7 Daily Energy Consumption for SVO.RC.M for Chicago

SVO.RC.M­HoustonEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.8 Daily Energy Consumption for SVO.RC.M for Houston

SVO.RC.M­Los AngelesEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.9 Daily Energy Consumption for SVO.RC.M for Los Angeles

**D­26**

### SVO.RC.M­MemphisEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.10 Daily Energy Consumption for SVO.RC.M for Memphis

VCT.RC.M­BaltimoreEnergyConsumption(kWh/Day) 40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a s e D i r E l e c

Eff Level 0 Eff Level 3 Eff Level 5 Eff Level 6



# Figure D.6.11 Daily Energy Consumption for VCT.RC.M for Baltimore

VCT.RC.M­BaltimoreEnergyConsumption(kWh/Day) 40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a s e D i r E l e c

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7



# Figure D.6.12 Daily Energy Consumption for VCT.RC.M for Chicago

**D­27**

### VCT.RC.M­Houston

0 10 20 30 40AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c



# Figure D.6.13 Daily Energy Consumption for VCT.RC.M for Houston

VCT.RC.M­Los Angeles

0 10 20 30 40AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c



# Figure D.6.14 Daily Energy Consumption for VCT.RC.M for Los Angeles

VCT.RC.M­Memphis

0 10 20 30 40AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c

`



# Figure D.6.15 Daily Energy Consumption for VCT.RC.M for Memphis

**D­28**EnergyConsumption(kWh/Day) 8

7

6

5

4

3

2

1

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5 CompElec

C a s e D i r E l e c Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5



# Figure D.6.16 Daily Energy Consumption for HZO.RC.M for Baltimore

HZO.RC.M­ChicagoEnergyConsumption(kWh/Day) 9

8

7

6

5

4

3

2

1

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a se D i r E l e c 

### HZO.RC.M­BaltimoreEnergyConsumption(kWh/Day) 9

8

7

6

5

4

3

2

1

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering 

# Figure D.6.17 Daily Energy Consumption for HZO.RC.M for Chicago

HZO.RC.M­Houston

CompElec

CaseDirElec

Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5



# Figure D.6.18 Daily Energy Consumption for HZO.RC.M for Houston

**D­29**

### HZO.RC.M­Los AngelesEnergyConsumption(kWh/Day) 9

8

7

6

5

4

3

2

1

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5 CompElec

C a s e D i r E l e c



# Figure D.6.19 Daily Energy Consumption for HZO.RC.M for Los Angeles

HZO.RC.M­MemphisEnergyConsumption(kWh/Day) 9

8

7

6

5

4

3

2

1

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5 CompElec

C a s e D i r E l e c



# Figure D.6.20 Daily Energy Consumption for HZO.RC.M for Memphis

SOC.RC.M­BaltimoreEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a se D i r E l e c

Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.6.21 Daily Energy Consumption for SOC.RC.M for Baltimore

**D­30**EnergyConsumption(kWh/Day) Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.6.23 Daily Energy Consumption for SOC.RC.M for Houston

SOC.RC.M­Los Angeles

CompElec

CaseDirElec Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.6.22 Daily Energy Consumption for SOC.RC.M for Chicago

SOC.RC.M­Houston

CompElec

CaseDirElecEnergyConsumption(kWh/Day) 60

50

40

30

20

10

0EnergyConsumption(kWh/Day)

60

50

40

30

20

10

0 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a s e D i r E l e cAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering 

### SOC.RC.M­Chicago

Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.6.24 Daily Energy Consumption for SOC.RC.M for Los Angeles

**D­31**Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.6.25 Daily Energy Consumption for SOC.RC.M for Memphis

VOP.RC.L­Baltimore



# Figure D.6.26 Daily Energy Consumption for VOP.RC.L for Baltimore

VOP.RC.L­ChicagoEnergyConsumption(kWh/Day)EnergyConsumption(kWh/Day)EnergyConsumption(kWh/Day)

160

140

120

100

80

60

40

20

0 160

140

120

100

80

60

40

20

0 60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e cAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e cAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering CompElec

C a s e D i r E l e c 

### SOC.RC.M­Memphis



# Figure D.6.27 Daily Energy Consumption for VOP.RC.L for Chicago

**D­32**

### VOP.RC.L­HoustonEnergyConsumption(kWh/Day) 160

140

120

100

80

60

40

20

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.28 Daily Energy Consumption for VOP.RC.L for Houston

VOP.RC.L­Los AngelesEnergyConsumption(kWh/Day) 160

140

120

100

80

60

40

20

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.29 Daily Energy Consumption for VOP.RC.L for Los Angeles

VOP.RC.L­MemphisEnergyConsumption(kWh/Day) 160

140

120

100

80

60

40

20

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6 CompElec

C a s e D i r E l e c



# Figure D.6.30 Daily Energy Consumption for VOP.RC.L for Memphis

**D­33**

### VCT.RC.L­BaltimoreEnergyConsumption(kWh/Day) 90

80

70

60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7 CompElec

C a s e D i r E l e c



# Figure D.6.31 Daily Energy Consumption for VCT.RC.L for Baltimore

VCT.RC.L­ChicagoEnergyConsumption(kWh/Day) 90

80

70

60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7 CompElec

C a s e D i r E l e c



# Figure D.6.32 Daily Energy Consumption for VCT.RC.L for Chicago

VCT.RC.L­HoustonEnergyConsumption(kWh/Day) 90

80

70

60

50

40

30

20

10

0AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7 CompElec

C a s e D i r E l e c



# Figure D.6.33 Daily Energy Consumption for VCT.RC.L for Houston

**D­34**

### VCT.RC.L­Los Angeles

0 10 20 30 40 50 60 70 80 90AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c

`



# Figure D.6.34 Daily Energy Consumption for VCT.RC.L for Los Angeles

VCT.RC.L­Memphis

0 10 20 30 40 50 60 70 80 90AnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.EngineeringAnnualSim.Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7EnergyConsumption(kWh/Day)

CompElec

C a s e D i r E l e c



# Figure D.6.35 Daily Energy Consumption for VCT.RC.L for Memphis

**D­35**

# D.7 COMPARISON OF DAILY ENERGY SAVINGS BETWEEN SIMULATION

RESULTS AND ENGINEERING ANALYSIS

VOP.RC.M

0 5 10 15 20 25EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis

Engineering



### Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.7.1 Daily Energy Savings for VOP.RC.M

SVO.RC.M

0 2 4 6 8 10 12 14 16 18EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis

Engineering



### Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.7.2 Daily Energy Savings for SVO.RC.M

VCT.RC.M

0 5 10 15 20 25 30EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis

Engineering

Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7



# Figure D.7.3 Daily Energy Savings for VCT.RC.M

**D­36**

## HZO.RC.M

Eff Level AD1 Eff Level AD2 Eff Level AD3 Eff Level AD5



# Figure D.7.4 Daily Energy Savings for HZO.RC.M

SOC.RC.M 0 1 2 3 4EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis

Engineering



### 0 4 8 12 16 20EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis

Engineering



### Eff Level AD1 Eff Level AD3 Eff Level AD4 Eff Level AD7



# Figure D.7.5 Daily Energy Savings for SOC.RC.M

VOP.RC.L

0 5 10 15 20 25 30 35EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis Engineering



### Eff Level AD1 Eff Level AD3 Eff Level AD5 Eff Level AD6



# Figure D.7.6 Daily Energy Savings for VOP.RC.L

**D­37**

## VCT.RC.L

0 5 10 15 20 25 30 35 40EnergySavings(kWh/Day) Annual Sim._Baltimore

Annual Sim._Chicago

Annual Sim._Houston

Annual Sim._Los Angeles

Annual Sim._Memphis Engineering



### Eff Level AD1 Eff Level AD4 Eff Level AD6 Eff Level AD7



# Figure D.7.7 Daily Energy Savings for VCT.RC.L

**D­38**

# D.8 COMPARISON OF ENERGY SAVINGS BETWEEN REFRIGERATION

SYSTEM AND WHOLE BUILDING

Energy Savings for Baltimore

(Ref. System versus Whole Building) 2500EnergySavings(MBtu)



### 2000

1500

1000

500

0 Ref. System

Whole Building

Level B Level C Level D



# Figure D.8.1 Daily Energy Savings for Baltimore (Refrigeration System versus Whole

Building)

Energy Savings for Chicago

(Ref. System versus Whole Building) 2500EnergySavings(MBtu)



### 2000

1500

1000

500

0 Ref. System

Whole Building

Level B Level C Level D



# Figure D.8.2 Daily Energy Savings for Chicago (Refrigeration System versus

Whole Building)

Energy Savings for Houston

(Ref. System versus Whole Building) 2500EnergySavings(MBtu)



### 2000

1500

1000

500

0

Level B Level C Level D Ref. System

Whole Building



# Figure D.8.3 Daily Energy Savings for Houston (Refrigeration System versus

Whole Building)

**D­39**

## Energy Savings for Los Angeles

(Ref. System versus Whole Building) 2500

Ref. SystemEnergySavings(MBtu)



### 2000

1500

1000

500

0 Whole Building

Level B Level C Level D



# Figure D.8.4 Daily Energy Savings for Los Angeles (Refrigeration System versus

Whole Building)

Energy Savings for Memphis

(Ref. System versus Whole Building) 2500EnergySavings(MBtu)



### 2000

1500

1000

500

0

Level B Level C Level D Ref. System

Whole Building



# Figure D.8.5 Daily Energy Savings for Memphis (Refrigeration System versus

Whole Building)

**D­40**