### Cunningham,James From: Sent: Michael VANDERHOOFT <MVANDERHOOFT@westech-inc.com> Tuesday, March 15, 2011 3:39 PM To: Cunningham, James Subject: RE: API budget proposal for EPA Project study 1110042
PartA: 38,000 Part B: 175,000 Part C: 225,000 From: Cunningham, James [mailto:jcunningham@rti.org] 

### Sent: Tuesday, March 15, 2011 12:53 PM To: Michael VANDERHOOFT Subject: RE: API budget proposal for EPA Project study 1110042 Michael, I'vefinally have gotten backtothis projectand have aquestion aboutyourquote.Could you please break-outthecost ofthecovers? A reply emailwould be fine, you don'tneed to modifythe quote. Thanks! James From: Michael VANDERHOOFT [mailto:MVANDERHOOFr@westech-inc.com] 

### Sent: Friday, February 04, 20111:32 PM To: Cunningham, James Cc: Lee WEBB; Floyd GRIFFITHS; CindyACORD Subject: RE: API budget proposal for EPA Project study 1110042 James, 1 just realized that I had mypricing inverted between itemA and itemC, Attached isthecorrected proposal,sorryformy dyslexia. Michael Vanderhooft, Applications Engineer Westech Engineering Phone/fax: 801-290-1919 mvanderhooft@westech-inc.com



## -------------------------------------------- From: Michael VANDERHOOFT 

### Sent: Friday, February 04, 201111:24 AM To: 'Cunningham, James' Cc: Lee WEBB; Floyd GRIFFITHS; Cindy ACORD Subject: API budget proposal for EPA Project study 1110042 James, Myname is MichaelVanderhooftand I have been workingwith Lee Webb regardingtheAPI Oil WaterSeparator units thatyou requested. I have attachedWesTech's budget proposal. Please let me know ifyou have anyquestions regarding it, or ifyou need anyadditional detailson the listed components. I've also attached aGA drawingforyour reference. Michael Vanderhooft, Applications Engineer Westech Engineering 1Phone/fax: 801-290-1919 mvanderhooft@westech-inc.com
From: Cunningham, James [mailto:jcunningham@rti.org] 

### Sent: Tuesday, January 25, 2011 9:49 AM 

### To: Lee WEBB 

### Subject: RE: api info Lee, No, but ifyou need one howabout 100mgjl? James From: Lee WEBB [mailto:LWEBB@westech-inc.com] 

### Sent: Tuesday, January 25, 201111:38AM 

### To: Cunningham, James Cc: Floyd GRIFFITHS 

### Subject: RE: api info James, Doyou have atargetTSS forthese designs? Lee Webb Applications Engineer WesTech Engineering, Inc. 3625 South WestTemple Salt Lake City, 

### UT 84115-4523 Phone: (801) 290-6427 Fax: (801) 265-1080 E-mail: LWebb@Westech-inc.com From: Cunningham, James [mailto:jcunningham@rti.org] 

### Sent: Tuesday, January 25, 2011 9:13 AM 

### To: Lee WEBB 

### Subject: api info Lee, Please find belowthe informationyou will need to design theoil-waterseparatorswediscussed. Please let me know if you need additional information. Flowrate, MGD 0.6, 5, 7 Temp., Deg. F 85 Oil Specific Gravity 0.92 TDS, mgjl 2170 Redundancy N+1
James H. Cunningham, Ph.D. SeniorResearch Environmental Engineer RTIInternational 919.541.8834 Email:jcunninqham@rti.orq 2

### Budget Proposal For: 

### EPA Project Equipment: 

### RectangularOil Water Separators Represented 

## By: EmoryWilson Industrial

Utah ·.Michael Vanderhooft IGlenn Thomas**,,.~,..,nnnP:** 

### {801)265-1000 mvanderhooft@westech-inc.com gthomas@westech-inc.com WesTech Proposal: 1110042 Date: February4, 2011

# WEsTEcH BUDGET PRICING Unless otherwise indicated, prices listed below are for equipment only.

ITEM EQUIPMENT



### A Two (2) 8' Wide x 46' Long Rectangular Oil Water Separators. WesTech Model OWSR6S B Seven (7) 10' Wide x 52' Long Rectangular Oil Water Separators. WesTech Model OWSR6S 

# c Eleven (11) 9' Wide x 48' Long Rectangular Oil WaterSeparators. WesTech Model OWSR6S *Budget pricing is 

### +1-20%

Project: EPA Project Proposal Number: 1110042 

### PRICE (U.S. 

### $) $ 410,000.00 * 

### $ 1,750,000.00 * 

### $2,350,000.00*

Page2 of 7 Date: February 4, 2011

# WEsTEcH· EQUIPMENT DESCRIPTION ITEM A: Two (2) 8' Wide x 46' Long Rectangular Oil Water Separators. WesTech Model OWSR6S. General Each OWS unit is designed for an influent flow rate of 417 gpm, a degree API of 21, a minimum temperature of 85o 

### F and a minimum globule size to be removed of 0.015 em. EACH UNIT FURNISHED COMPLETEWITH THE FOLLOWING COMPONENTS:

- One (1) 8' Wide x 46' long flat bottom, shop built carbon steel tank fabricated of carbon steel plate with suitable reinforcements.

- One (1) removable, fixed steel tank cover.

- One (1) 2' long clearwell integral to the tank

- One (1) skimmer 

### I scraper drive unit directly coupled to the drive shaftwith a VFD rated V2 hp 230/460 VAC, 3 phase, TEFC motor.

- Four (4) shafts, one (1) drive and three (3) tail, each constructed of carbon steel with wall bearings.

- One (1) carbon steel effluent baffle with adjustable overflow weir integral to the tank.

- One (1) slotted pipe skimmerforthe removal of surface oil.

- Eight (8) non-metallic sprocketswith non-metallicchain.

- Eighteen (18) FRP flight skimmer

### Iscraper assemblieswith wipers.

- One (1) electric control panel forcontrol of proposed equipment.

- One (1) lot304 stainless steel hardware and fasteners forall supplied equipment.

- Ferrous metal will be blasted with one (1) coat of epoxy primer and one (1) coat of epoxy top coat.

- Field service oftwo (2) trips forfour (4) days for inspection, start-up and training.

Project: EPA Project Proposal Number: 1110042 Page 3 of 7 Date: February4, 2011

# WEsTEcH ITEM 

### 8: Seven 

### (7) 10' Wide x 52' Long Rectangular Oil Water Separators. WesTech Model OWSR6S 

### General Each OWS unit is designed for an influentflow rate of 580 gpm, a degree API of21, a minimum temperature of 85° F and a minimum globule size to be removed of 0.015 em. EACH UNIT FURNISHED COMPLETEWITH THE FOLLOWING COMPONENTS:

- One (1) 10' Wide x 52' long flat bottom, shop built carbon steel tank fabricated of carbon steel plate with suitable reinforcements.

- One (1) removable, fixed steel tankcover.

- One (1) 2' long clearwell integral to the tank

- One (1) skimmer

### I scraper drive unit directly coupled to the drive shaftwith a VFD rated Y2 hp 2301460 VAC, 3 phase,TEFC motor.

- Four (4) shafts, one (1) drive and three (3) tail, each constructed of carbon steel with wall bearings.

- One (1) carbon steel effluent baffle with adjustable overflow weir integral to the tank.

- One (1) slotted pipe skimmerforthe removal of surface oil.

- Eight (8) non-metallic sprockets with non-metallicchain.

- Twenty (20) FRP flight skimmer

### Iscraperassemblies with wipers.

- One (1) electric control panelfor control of proposed equipment.

- One (1) lot304 stainless steel hardware and fasteners for all supplied equipment.

- Ferrous metal will be blasted with one (1) coat of epoxy primer and one (1) coat of epoxy top coat.

- Field service oftwo (2) tripsforfour (4) daysfor inspection, start-up and training.

Project: EPA Project Proposal Number: 1110042 Page 4 of 7 Date: February4, 2011ITEM C: Eleven (11) 9' Wide x 48' Long Rectangular Oil Water Separators. WesTech Model OWSRSS General Each OWS unit is designed for an influent flow rate of 487 gpm, a degree API of 21, a minimum temperature of 85° F and a minimum globule size to be removed of 0.015 em. EACH UNIT FURNISHED COMPLETEWITH THE FOLLOWING COMPONENTS:

- One (1) 9' Wide x 48' long flat bottom, shop built carbon steel tank fabricated of carbon steel plate with suitable reinforcements.

- One (1) removable, fixed steel tank cover.

- One (1) 2' long clearwell integralto the tank

- One (1) skimmer 

### I scraper drive unit directly coupled to the drive shaft with a VFD rated Y2 hp 2301460 VAC, 3 phase, TEFC motor.

- Four (4) shafts, one (1) drive and three (3) tail, each constructed of carbon steel with wall bearings.

- One (1) carbon steel effluent baffle with adjustable overflow weir integral to the tank.

- One (1) slotted pipe skimmerforthe removal of surface oil.

- Eight (8) non-metallic sprocketswith non-metallicchain.

- Nineteen (19) FRP flight skimmer

### Iscraperassemblieswith wipers.

- One (1) electric control panel for control of proposed equipment.

- One (1) lot304 stainless steel hardware and fasteners for all supplied equipment.

- Ferrous metal will be blasted with one (1) coat of epoxy primer and one (1) coat of epoxytop coat.

- Field service oftwo (2) trips forfour (4) daysfor inspection, start-up and training. NOTE: ANY ITEM NOT LISTED ABOVETO BE FURNISHED BYOTHERS. These proposal sections have been reviewed for accuracy and approved for issue:

# By:_~_t,c_·**J,_~_J_V._~--4~~-** Project: EPA Project Proposal Number: 1110042 Date: February 4, 2011 Page 5 of 7 Date: February4, 2011

# WEsTEcH

.• •• t**~·** o:.· ":'' r r c-wt.o!: :.- ::.: ,•:· r • ..,-. 

### WESTECH TERMS Unless otherwise indicated, prices listed arefor equipment only. Prices are based on the estimated cost ofgoodsand services atthe budget proposal date. Future escalation is not included in the pricing. SalesTax: No salestaxes, use taxes, orduties have been included in ourpricing. Equipment Pavment.Terms: Termsfor equipment are 15percent paymentof the purchase price with submittal drawings, 35 percent upon release tofabrication, and 50 percent net 30 daysfrom shipment. Freight: NotQuoted. Schedule: Approval drawingswill be submitted within 4 to 6weeks after receipt and acceptance of purchase order. Shipment: Estimated shipmenttime is 18to 22 weeks, plus 1to 2 additional weeks pertank beyond the first, after approved shopdrawings are received in ouroffice.

Project: EPA Project Proposal Number: 1110042 Page 6 of 7 Date: February4, 2011' 

# . WESTECH 

# WARRANTY WesTech equipment is backed by WesTech's reputation as a quality manufacturer, and by manyyears ofexperience in the design of reliable equipment. Equipment manufactured or sold by WesTech Engineering, Inc., once paid for in full, is backed bythe following warranty: For the benefit of the original user, WesTech warrants all new equipment manufactured by WesTech Engineering, Inc. to be free from defects in material and workmanship, and will replace or repair, F.O.B. its factories or other location designated by it, any part or parts returned to it which WesTech's examination shall show to have failed under normal use and service by the original user within one (1) year following initial start-up, or eighteen (18) months from shipment to the purchaser, whichever occurs first. Such repair or replacement shall be free of charge for all items except for those items such as resin, filter media and the like that are consumable and normally replaced during maintenance, with respect to which, repairor replacement shall be subjectto a pro-rata charge based upon WesTech's estimate of the percentage of normal service life realized from the part. WesTech's obligation under this warranty is conditioned upon its receiving prompt notice of claimed defects, which shall in no event be laterthan thirty (30) days following expiration ofthe warranty period, and is limited to repairor replacement as aforesaid. THIS WARRANTY IS EXPRESSLY MADE BY WESTECH AND ACCEPTED BY PURCHASER IN LIEU OF ALL OTHER WARRANTIES, INCLUDING WARRANTIES OF MERCHANTABILITY AND FITNESS FOR PARTICULAR PURPOSE, WHETHER WRITIEN, ORAL, EXPRESS, IMPLIED, OR STATUTORY. WESTECH NEITHER ASSUMES NOR AUTHORIZES ANY OTHER PERSON TO ASSUME FOR iT ANY OTHER LIABILITY WITH RESPECT TO ITS EQUIPMENT. WESTECH SHALL NOT BE LIABLE FOR NORMALWEAR AND TEAR, CORROSION, OR ANY CONTINGENT, INCIDENTAL, OR CONSEQUENTIAL DAMAGE OR EXPENSE DUE TO PARTIAL OR COMPLETE INOPERABILITY OF ITS EQUIPMENT FOR ANY REASON WHATSOEVER. This warranty shall not apply to equipment or parts thereof which have been altered or repaired outside of a WesTech factory, or damaged by improper installation, application, or maintenance, orsubjected to misuse, abuse, neglect, accident, or incomplete adherence to all manufacturer's requirements, including, but not limited to, Operations & Maintenance Manual guidelines & procedures. Thiswarranty applies onlyto equipment made orsold byWesTech Engineering, Inc. WesTech Engineering, Inc. makes no warranty with respect to parts, accessories, or components purchased by the customer from others. The warranties which apply to such items are those offered bytheir respective manufacturers.

OF·00·032E

Project: EPA Project Proposal Number: 1110042 Rev. 08/18105

Page 7 of 7 Date: February4, 2011