Name: Jeffrey Walker

Title: Environmental Manager

Company: Cedar Bay Generating Plant

Sign Date: 7/22/2010

Name: Stephen Webb

Title: Air Testing Coordinator

Company: Coastal Air Consulting Inc.

Sign Date: 7/22/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Cedar Bay Generating Plant, ORIS Code 10672

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, January 22, 2011 Page 1 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Facility Information:

Cedar Bay Generating Plant (ORIS Code:10

9640 Eastport Road(32218)

P.O.Box 26324

Jacksonville Fl 32226

Contact: Jeff Walker

Phone: 904-696-1547

Fax: 904-751-7320

Email: jeffwalker@cogentrix.com

Testing Company:

Coastal Air Consulting

245 West Ohio Avenue

Suite A

Lake Helen Fl 32744

Contact: Steven Webb

Phone: 386-451-0169

Fax:

Email: coastalair123@aol.com

Air Permit Number:

310337-016-AV

Permitted Source ID/Name:

CBC

Permitted Maximum Process Rate:

104000 lbs/hr

Max. Normal Operation Process Rate:

90000 lbs/hr

Target Process Test Rate

85000 lbs/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

CFB w/limestone injection for acid gas control, SNCR for Nox control, baghouse with pulse air for particulates

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #: 110000362018

SCC / Description 10100218 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Atmospheric Fluidized Bed Combustion: Circulating Bed (Bitum. Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

duct post 

baghouse

0 109 126.6 117 237 105 6 24

Regulation Description Compound Limit Unit

Sulfur Dioxide 0.3 lb/million BTU 

using CO2

Nitrogen oxides (NOx) 0.17 lb/million BTU 

using CO2

Carbon Monoxide 0.175 lb/million BTU 

using CO2

Total Particulate 0.018 lb/million BTU 

using CO2

Total PM10 0.018 lb/million BTU 

using CO2

Saturday, January 22, 2011 Page 2 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

N/A

Test Parameter Information:

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Total organic compounds 

(TOC)

duct post Method 25A 3 120 0

baghouse

duct post Hydrogen Fluoride Method 26A 3 180 0

baghouse

duct post Hydrogen Chloride Method 26A 3 180 0

baghouse

Inorganic (Aqueous) 

Condensible Part.

duct post OTM - 27/28 3 240 0

baghouse

duct post Filterable PM2.5 OTM - 27/28 3 240 0

baghouse

duct post Cobalt Method 29 3 240 0

baghouse

duct post Selenium Method 29 3 240 0

baghouse

duct post Nickel Method 29 3 240 0

baghouse

duct post Manganese Method 29 3 240 0

baghouse

duct post Lead Method 29 3 240 0

baghouse

duct post Arsenic Method 29 3 240 0

baghouse

duct post Chromium Method 29 3 240 0

baghouse

duct post Beryllium Method 29 3 240 0

baghouse

duct post Cadmium Method 29 3 240 0

baghouse

duct post Filterable Particulate Method 29 3 240 0

baghouse

duct post Antimony Method 29 3 240 0

baghouse

Saturday, January 22, 2011 Page 3 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Sampling / Stack Data Results Summary

Location duct post baghouse - Method 25A

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/18/2010

Run Start Time 9:47:00 AM 12:00:00 

PM

2:15:00 PM

Run Finish Time 11:47:00 AM 2:00:00 PM 4:15:00 PM

Carbon Dioxide, % 14.443 13.878 14.585 14.302

Oxygen, % 4.915 5.448 4.88 5.081

Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 8.4 7.6 7.9 7.967

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location duct post baghouse - Method 26A

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/18/2010

Run Start Time 9:47:00 AM 1:00:00 PM 4:15:00 PM

Run Finish Time 12:39:30 PM 3:52:30 PM 7:07:30 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 163.528 169.599 164.496 165.874

Moisture Content of Stack Gas, % 9.18 9.28 9.66 9.373

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.5 15.5 15.5 15.500

Oxygen, % 3.4 3.4 3.4 3.400

Average Stack Gas Temperature, °F 310.54 313.79 316.13 313.487

Dry Volumetric Flow Rate, dry scfm 246,196.7 255,241.7 247,026.6 249,488.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 416,338.7 433,932.9 423,008.4 424,426.667

Percent Isokinetic of Sampling Rate, % 103.7 103.8 104.0 103.833

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, January 22, 2011 Page 4 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Location duct post baghouse - Method 29

Average

Run Number 1 2 M5-3

Test Date 5/19/2010 5/19/2010 5/20/2010

Run Start Time 10:00:00 AM 2:28:00 PM 9:34:00 AM

Run Finish Time 1:50:00 PM 6:18:00 PM 1:24:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 220.177 224.948 201.728 215.618

Moisture Content of Stack Gas, % 8.76 8.45 8.22 8.477

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 12.7 12.7 12.8 12.733

Oxygen, % 5.9 5.8 6.1 5.933

Average Stack Gas Temperature, °F 303.67 315.83 304.38 307.960

Dry Volumetric Flow Rate, dry scfm 249,234.4 252,665.4 229,294.0 243,731.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 415,648.7 426,630.7 380,230.3 407,503.233

Percent Isokinetic of Sampling Rate, % 103.5 104.3 103.1 103.633

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location duct post baghouse - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 10:54:00 AM 10:02:00 

AM

3:36:00 PM

Run Finish Time 3:34:00 PM 2:31:00 PM 8:17:00 PM

Net Run Time, minutes 299.5 287.5 300.25

Dry Gas Meter Volume Sampled, dscf 101.791 96.838 100.719 99.783

Moisture Content of Stack Gas, % 0.00 0.00 0.00 0.000

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14.5 14.5 14.5 14.500

Oxygen, % 5 5 5 5.000

Average Stack Gas Temperature, °F 315.17 313.33 321.42 316.640

Dry Volumetric Flow Rate, dry scfm 278,603.7 267,961.9 278,343.6 274,969.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 430,310.5 412,601.3 433,070.4 425,327.400

Percent Isokinetic of Sampling Rate, % 81.7 84.2 80.7 82.200

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, January 22, 2011 Page 5 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Emissions Summary

Location: duct post baghouse - Method 25A

Compound: Total organic compounds (TOC)

Average

Run 1 2 3

ppm 6.05E-01 6.49E-01 5.34E-01 0.596

ppm@7%O2 5.26E-01 5.84E-01 4.63E-01 0.524

Location: duct post baghouse - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 310.487 326.298 323.771 320.185

lb/mmBtuCO2 4.86E-02 4.93E-02 5.04E-02 0.049

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.318 0.323 0.329 0.323

lb/mmBtuCO2 4.98E-05 4.88E-05 5.12E-05 0.000

Location: duct post baghouse - Method 29

Compound: Antimony

Average

RunNumber 1 2 M5-3

Mass_mg 0.000955 0.000321 0.000397 0.001

lb/mmBtuCO2 1.36E-07 4.46E-08 6.10E-08 0.000

Compound: Arsenic

Average

RunNumber 1 2 M5-3

Mass_mg 0.00364 0.003233 0.003933 0.004

lb/mmBtuCO2 5.17E-07 4.49E-07 6.04E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 M5-3

Mass_mg 0.000944 0.000979 0.000931 0.001

lb/mmBtuCO2 1.34E-07 1.36E-07 1.43E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 M5-3

Mass_mg 0.004477 0.001296 0.004497 0.003

lb/mmBtuCO2 6.35E-07 1.80E-07 6.91E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 M5-3

Mass_mg 0.01804 0.0149 0.01346 0.015

lb/mmBtuCO2 2.56E-06 2.07E-06 2.07E-06 0.000

Saturday, January 22, 2011 Page 6 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Process Run Data

Compound: Cobalt

Average

RunNumber 1 2 M5-3

Mass_mg 0.003282 0.003421 0.003458 0.003

lb/mmBtuCO2 4.66E-07 4.75E-07 5.31E-07 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 M5-3

Mass_mg 25.6 115.6 129.2 90.133

lb/mmBtuCO2 3.63E-03 1.61E-02 1.99E-02 0.013

Compound: Lead

Average

RunNumber 1 2 M5-3

Mass_mg 0.00736 0.00637 0.00626 0.007

lb/mmBtuCO2 1.04E-06 8.85E-07 9.62E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 M5-3

Mass_mg 0.01117 0.01082 0.012556 0.012

lb/mmBtuCO2 1.59E-06 1.50E-06 1.93E-06 0.000

Compound: Nickel

Average

RunNumber 1 2 M5-3

Mass_mg 0.01508 0.01221 0.0092 0.012

lb/mmBtuCO2 2.14E-06 1.70E-06 1.41E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 M5-3

Mass_mg 0.0027 0.00295 0.00343 0.003

lb/mmBtuCO2 3.83E-07 4.10E-07 5.27E-07 0.000

Location: duct post baghouse - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 0.005 0.003 0.003 0.004

lb/mmBtuCO2 1.34E-06 8.48E-07 8.15E-07 0.000

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 71.4 13.9 6 30.433

lb/mmBtuCO2 1.92E-02 3.93E-03 1.63E-03 0.008

Saturday, January 22, 2011 Page 7 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 39.5 Tons/hr 40

1 heat input 1050 lbs/mmBtu 1000

1 steam flow 790 klbs/hr 780

Run Name Value UOM Comments

Target

Value

1 FLUID BED DRY SCRUBBER 0.19 lbs/mmbtu 0.25

1 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

0.16 lbs/mmBtu 0.16

1 BAGHOUSE 3 opacity 5

Run Name Value UOM Comments

1 btu value of coal 12303 btu/lb

Saturday, January 22, 2011 Page 8 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Sampling / Stack Data Results Detail

Location duct post baghouse - Method 25A

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/18/2010

Run Start Time 9:47:00 AM 12:00:00 PM 2:15:00 PM

Run Finish Time 11:47:00 AM 2:00:00 PM 4:15:00 PM

Carbon Dioxide, % 14.443 13.878 14.585 14.302

Oxygen, % 4.915 5.448 4.88 5.081

Fuel Factor 1.11 1.11 1.1

Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 8.4 7.6 7.9 7.967

Analyzer Make Vig Vig Vig

Analyzer Model 20 20 20 20.000

Analyzer Serial Number 1591203 1591203 1591203 1,591,203.0

00

Operating Range 20 20 20 20.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID CC-231298 CC-231298 CC-231298

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB-0017527 EB-0017527 EB-0017527

Calibration Pre High Cylinder Instrument Response 6.1 6.1 6.1 6.100

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-231298 CC-231298 CC-231298

Calibration Post Zero Cylinder Instrument Response 0.1 0.1 0.1 0.100

Calibration Post Zero Cylinder Bias 0.5 0.5 0.5 0.500

Calibration Post Zero Cylinder Drift 0.5 0.5 0.5 0.500

Calibration Post High Cylinder ID EB-0017527 EB-0017527 EB-0017527

Calibration Post High Cylinder Instrument Response 6.1 6 5.9 6.000

Calibration Post High Cylinder Bias 0 -0.5 -1 -0.500

Calibration Post High Cylinder Drift 0 0.5 1 0.500

Cavg 0.67 0.71 0.58 0.653

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.6046 0.649 0.5336 0.596

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Saturday, January 22, 2011 Page 9 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Location duct post baghouse - Method 26A

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/18/2010

Run Start Time 9:47:00 AM 1:00:00 PM 4:15:00 PM

Run Finish Time 12:39:30 PM 3:52:30 PM 7:07:30 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.988 0.988 0.988 0.988

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 2.89 3.13 2.96 2.993

Dry Gas Meter Volume Sampled, cubic feet 172.969 181.668 177.487 177.375

Average Dry Gas Meter Temperature, °F 95.33 102.71 106.58 101.540

Dry Gas Meter Volume Sampled, dscf 163.528 169.599 164.496 165.874

Total Moisture Liquid collected, g 350.9 368.7 373.5 364.367

Volume of Water Vapor, standard cubic feet 16.52 17.35 17.58 17.150

Moisture Content of Stack Gas, % 9.18 9.28 9.66 9.373

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9082 0.9072 0.9034 0.906

Carbon Dioxide, % 15.5 15.5 15.5 15.500

Oxygen, % 3.4 3.4 3.4 3.400

Carbon Monoxide & Nitrogen, % 81.1 81.1 81.1 81.100

Fuel Factor 1.13 1.13 1.13

Dry Molecular Weight, lb/lb-Mole 30.62 30.62 30.62 30.620

Wet Molecular weight, lb/lb-Mole 29.46 29.45 29.40 29.437

Flue Gas Static Pressure, inches of H2O -20 -20 -20 -20.000

Absolute Flue Gas Pressure, inches of Mercury 28.43 28.43 28.43 28.430

Average Stack Gas Temperature, °F 310.54 313.79 316.13 313.487

Average Velocity Head, inches of H2O 1.1052810136

8768

1.195079069

13107

1.130446001

71903

1.144

Average Stack Gas Velocity, feet/second 72.41 75.47 73.57 73.817

Stack Cross-Sectional Area, square feet 95.829 95.829 95.829 95.829

Dry Volumetric Flow Rate, dry scfm 246,196.7 255,241.7 247,026.6 249,488.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 416,338.7 433,932.9 423,008.4 424,426.667

Percent Isokinetic of Sampling Rate, % 103.7 103.8 104.0 103.833

Percent Excess Air, % 18.9 18.9 18.9 18.900

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 126.6 126.6 126.6

Rectangular Duct Length, inches 109 109 109

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, January 22, 2011 Page 10 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Location duct post baghouse - Method 29

Average

Run Number 1 2 M5-3

Test Date 5/19/2010 5/19/2010 5/20/2010

Run Start Time 10:00:00 AM 2:28:00 PM 9:34:00 AM

Run Finish Time 1:50:00 PM 6:18:00 PM 1:24:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.988 0.988 0.988 0.988

Barometric Pressure, inches of Mercury 29.91 29.91 29.93 29.917

Average Orifice Meter Differential, inches H2O 2.89 3.01 2.42 2.773

Dry Gas Meter Volume Sampled, cubic feet 231.993 240.205 215.097 229.098

Average Dry Gas Meter Temperature, °F 93.38 100.98 99.73 98.030

Dry Gas Meter Volume Sampled, dscf 220.177 224.948 201.728 215.618

Total Moisture Liquid collected, g 449.3 441.1 383.8 424.733

Volume of Water Vapor, standard cubic feet 21.15 20.76 18.07 19.993

Moisture Content of Stack Gas, % 8.76 8.45 8.22 8.477

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9124 0.9155 0.9178 0.915

Carbon Dioxide, % 12.7 12.7 12.8 12.733

Oxygen, % 5.9 5.8 6.1 5.933

Carbon Monoxide & Nitrogen, % 81.4 81.5 81.1 81.333

Fuel Factor 1.18 1.19 1.16

Dry Molecular Weight, lb/lb-Mole 30.27 30.26 30.29 30.273

Wet Molecular weight, lb/lb-Mole 29.20 29.22 29.28 29.233

Flue Gas Static Pressure, inches of H2O -20 -20 -20 -20.000

Absolute Flue Gas Pressure, inches of Mercury 28.44 28.44 28.46 28.447

Average Stack Gas Temperature, °F 303.67 315.83 304.38 307.960

Average Velocity Head, inches of H2O 1.1018524656

7954

1.143672380

84561

0.924378582

032605

1.057

Average Stack Gas Velocity, feet/second 72.29 74.20 66.13 70.873

Stack Cross-Sectional Area, square feet 95.829 95.829 95.829 95.829

Dry Volumetric Flow Rate, dry scfm 249,234.4 252,665.4 229,294.0 243,731.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 415,648.7 426,630.7 380,230.3 407,503.233

Percent Isokinetic of Sampling Rate, % 103.5 104.3 103.1 103.633

Percent Excess Air, % 37.8 36.9 39.8 38.167

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 126.6 126.6 126.6

Rectangular Duct Length, inches 109 109 109

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, January 22, 2011 Page 11 of 12
Cedar Bay Generating Plant, ORIS Code 10672

7/22/2010

Location duct post baghouse - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 10:54:00 AM 10:02:00 AM 3:36:00 PM

Run Finish Time 3:34:00 PM 2:31:00 PM 8:17:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 299.5 287.5 300.25

Nozzle Diameter, inches 0.162 0.162 0.162 0.162

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.948 0.948 0.948 0.948

Barometric Pressure, inches of Mercury 29.91 29.93 29.93 29.923

Average Orifice Meter Differential, inches H2O 0.40 0.40 0.40 0.400

Dry Gas Meter Volume Sampled, cubic feet 112.995 107.827 112.333 111.052

Average Dry Gas Meter Temperature, °F 96.00 98.08 99.00 97.693

Dry Gas Meter Volume Sampled, dscf 101.791 96.838 100.719 99.783

Total Moisture Liquid collected, g 0 0 0 0.000

Volume of Water Vapor, standard cubic feet 0.00 0.00 0.00 0.000

Moisture Content of Stack Gas, % 0.00 0.00 0.00 0.000

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 1 1 1 1.000

Carbon Dioxide, % 14.5 14.5 14.5 14.500

Oxygen, % 5 5 5 5.000

Carbon Monoxide & Nitrogen, % 80.5 80.5 80.5 80.500

Fuel Factor 1.10 1.10 1.10

Dry Molecular Weight, lb/lb-Mole 30.52 30.52 30.52 30.520

Wet Molecular weight, lb/lb-Mole 30.52 30.52 30.52 30.520

Flue Gas Static Pressure, inches of H2O -20 -20 -20 -20.000

Absolute Flue Gas Pressure, inches of Mercury 28.44 28.46 28.46 28.453

Average Stack Gas Temperature, °F 315.17 313.33 321.42 316.640

Average Velocity Head, inches of H2O 1.2162039893

3752

1.121436272

80343

1.222705565

37557

1.187

Average Stack Gas Velocity, feet/second 74.84 71.76 75.32 73.973

Stack Cross-Sectional Area, square feet 95.829 95.829 95.829 95.829

Dry Volumetric Flow Rate, dry scfm 278,603.7 267,961.9 278,343.6 274,969.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 430,310.5 412,601.3 433,070.4 425,327.400

Percent Isokinetic of Sampling Rate, % 81.7 84.2 80.7 82.200

Percent Excess Air, % 30.8 30.8 30.8 30.800

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 126.6 126.6 126.6

Rectangular Duct Length, inches 109 109 109

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, January 22, 2011 Page 12 of 12