Name: Kevin Holbrooks

Title: Director, Environmental Compliance

Company: Jacksonville Electric Authority

Sign Date:

Name: Carl Vineyard

Title: Utility MACT Program Manager

Company: Grace Consulting, Inc.

Sign Date: 8/5/2010

Permitted Facility Representative / Date Testing Company Representative / Date

JEA, Northside Station, Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, February 04, 2011 Page 1 of 35
JEA, Northside Station, Unit 1

Facility Information:

Northside Station, Unit 1

4377 Heckscher Drive

Jacksonville FL 32226

Contact: Kevin Holbrooks

Phone: 904-665-4540

Fax: 904-665-4530

Email: Holbke@JEA.com

Testing Company:

Grace Consulting, Inc.

510 Dickson Street

Wellington OH 44090

Contact:Carl Vineyard

Phone: 440-647-6672

Fax: 440-647-6673

Email: carlvineyard@gcitest.com

Air Permit Number:

667

Permitted Source ID/Name:

1 JEA Northside Generating Station

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Upstream Downstream attached.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1203100045 FRS #: 11003764106

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Unit 1 Stack 180 0 0 0 3600 1548 4 48

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Unit 1 Stack Carbon Monoxide Method 10 3 120 0

Unit 1 Stack 2,3,7,8-TCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8-PeCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Friday, February 04, 2011 Page 2 of 35
JEA, Northside Station, Unit 1

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

The HCN was sampled using CTM 033 with 6 Normal NaOH and an additional impinger for one hour per the 

Unit 1 Stack OCDD Method 23 3 480 0

Unit 1 Stack 2,3,7,8-TCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8-PeCDF Method 23 3 480 0

Unit 1 Stack 2,3,4,7,8-PeCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Unit 1 Stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Unit 1 Stack OCDF Method 23 3 480 0

Unit 1 Stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Unit 1 Stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Unit 1 Stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Unit 1 Stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Unit 1 Stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Unit 1 Stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Unit 1 Stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Unit 1 Stack Method 23 3 480 0

Unit 1 Stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Unit 1 Stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Unit 1 Stack Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Unit 1 Stack Method 25A 3 120 0

Unit 1 Stack Hydrogen Chloride Method 26A 3 180 0

Unit 1 Stack Hydrogen Fluoride Method 26A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

Unit 1 Stack OTM - 27/28 3 360 0

Organic Condensible 

Particulate

Unit 1 Stack OTM - 27/28 3 360 0

Unit 1 Stack Total PM2.5 OTM - 27/28 3 360 0

Unit 1 Stack Filterable PM2.5 OTM - 27/28 3 360 0

Unit 1 Stack Cadmium Method 29 3 192 0

Unit 1 Stack Filterable Particulate Method 29 3 192 0

Unit 1 Stack Selenium Method 29 3 192 0

Unit 1 Stack Nickel Method 29 3 192 0

Unit 1 Stack Lead Method 29 3 192 0

Unit 1 Stack Chromium Method 29 3 192 0

Unit 1 Stack Manganese Method 29 3 240 0

Unit 1 Stack Beryllium Method 29 3 192 0

Unit 1 Stack Arsenic Method 29 3 192 0

Unit 1 Stack Antimony Method 29 3 192 0

Unit 1 Stack Cobalt Method 29 3 192 0

Unit 1 Stack Co2 Method 3A CO2 3 180 0

Unit 1 Stack O2 Method 3A O2 3 180 0

Unit 1 Stack Sulfur Dioxide Method 6C 3 180 0

Unit 1 Stack Nitrogen oxides (NOx) Method 7E 3 180 0

Friday, February 04, 2011 Page 3 of 35
JEA, Northside Station, Unit 1

clarification given by the USEPA.

Friday, February 04, 2011 Page 4 of 35
JEA, Northside Station, Unit 1

Friday, February 04, 2011 Page 5 of 35
JEA, Northside Station, Unit 1

Sampling / Stack Data Results Summary

Location Unit 1 Stack - Method 10

Average

Run Number 1 2 3

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 

AM

11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 

AM

1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9922 9921 9,887.667

Moisture, % 14.44 10.57 11.2 12.070

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - Method 23

Average

Run Number 1 2 3

Test Date 5/25/2010 5/26/2010 5/25/2010

Run Start Time 9:00:00 AM 11:50:00 

AM

7:45:00 AM

Run Finish Time 5:15:00 PM 8:05:00 PM 3:56:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 310.898 312.113 309.375 310.795

Moisture Content of Stack Gas, % 10.87 10.17 10.05 10.363

Moisture Saturation at Stack Gas Temperature, % 82.79 82.08 84.64 83.170

Carbon Dioxide, % 15.1 15.4 15.3 15.267

Oxygen, % 4.3 4.6 4.8 4.567

Average Stack Gas Temperature, °F 202.44 201.71 203.10 202.417

Dry Volumetric Flow Rate, dry scfm 583,207.1 591,972.3 585,074.4 586,751.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 824,799.6 835,084.4 827,662.4 829,182.133

Percent Isokinetic of Sampling Rate, % 105.1 104.0 104.3 104.467

F-Factor, dscfm/MMBtu @ %O2 9796 9913 9973 9,894.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 6 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 25A

Average

Run Number 1 2 3

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 

AM

11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 

AM

1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9923 9923 9,888.667

Moisture, % 14.44 10.57 11.2 12.070

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - Method 26A

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 

AM

11:30:00 AM

Run Finish Time 5:50:30 PM 11:10:30 

AM

2:42:30 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 112.619 112.207 113.249 112.692

Moisture Content of Stack Gas, % 10.30 8.31 9.62 9.410

Moisture Saturation at Stack Gas Temperature, % 78.71 100.00 99.58 92.763

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Average Stack Gas Temperature, °F 199.63 263.54 211.25 224.807

Dry Volumetric Flow Rate, dry scfm 584,556.2 600,500.4 603,512.5 596,189.700

Actual Wet Volumetric Flue Gas Flow Rate, acfm 824,057.4 906,866.0 858,092.7 863,005.367

Percent Isokinetic of Sampling Rate, % 101.3 98.3 98.7 99.433

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 7 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 29

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 12:41:00 PM 7:27:00 PM 1:34:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 159.765 163.044 159.448 160.752

Moisture Content of Stack Gas, % 11.00 10.85 10.75 10.867

Moisture Saturation at Stack Gas Temperature, % 75.68 74.43 77.35 75.820

Carbon Dioxide, % 15.6 15.2 15.2 15.333

Oxygen, % 4.8 4.8 4.7 4.767

Average Stack Gas Temperature, °F 197.73 197.10 198.81 197.880

Dry Volumetric Flow Rate, dry scfm 578,929.3 599,059.7 580,520.8 586,169.933

Actual Wet Volumetric Flue Gas Flow Rate, acfm 820,452.4 843,884.8 821,194.6 828,510.600

Percent Isokinetic of Sampling Rate, % 102.1 100.7 101.6 101.467

F-Factor, dscfm/MMBtu @ %O2 9695 9717 9896 9,769.333

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - Method 3A CO2

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 

AM

11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 

AM

2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Dry Volumetric Flow Rate, dry scfm 651252 654698 603555 636,501.667

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 8 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A CO2 3

Average

Run Number 4 5 6

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 2:43:00 PM 9:25:00 PM 3:30:00 PM

Carbon Dioxide, % 15.6 15.2 15.2 15.333

Oxygen, % 4.8 4.8 4.7 4.767

Dry Volumetric Flow Rate, dry scfm 666360 689792 692409 682,853.667

F-Factor, dscfm/MMBtu @ %O2 9695 9717 9896 9,769.333

Moisture, % 11.61 11 11.19 11.267

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - Method 3A CO2 3 6

Average

Run Number 7 8 9

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 

AM

11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 

AM

1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9922 9921 9,887.667

Moisture, % 14.44 10.57 11.2 12.070

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 9 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A O2

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 

AM

11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 

AM

2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Dry Volumetric Flow Rate, dry scfm 651252 654698 667844 657,931.333

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - Method 3A O2 3

Average

Run Number 4 5 6

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 2:43:00 PM 9:25:00 PM 3:30:00 PM

Carbon Dioxide, % 15.6 15.2 15.6 15.467

Oxygen, % 4.8 4.8 4.8 4.800

Dry Volumetric Flow Rate, dry scfm 666360 689792 666360 674,170.667

F-Factor, dscfm/MMBtu @ %O2 9695 9717 9896 9,769.333

Moisture, % 11.61 11 11.61 11.407

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 10 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A O2 3 6

Average

Run Number 7 8 9

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 

AM

11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 

AM

1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9922 9921 9,887.667

Moisture, % 14.44 10.57 11.2 12.070

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - Method 6C

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 

AM

11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 

AM

2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Dry Volumetric Flow Rate, dry scfm 651252 654698 667844 657,931.333

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 11 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 7E

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 

AM

11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 

AM

2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Dry Volumetric Flow Rate, dry scfm 651252 654698 667844 657,931.333

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Unit 1 Stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 2:43:42 PM 8:25:48 PM 3:30:36 PM

Net Run Time, minutes 360 360 360

Dry Gas Meter Volume Sampled, dscf 122.501 124.316 124.355 123.724

Moisture Content of Stack Gas, % 11.62 11.00 11.18 11.267

Moisture Saturation at Stack Gas Temperature, % 74.92 83.75 83.09 80.587

Carbon Dioxide, % 15.6 15.2 15.2 15.333

Oxygen, % 4.8 4.8 4.7 4.767

Average Stack Gas Temperature, °F 197.33 202.75 202.25 200.777

Dry Volumetric Flow Rate, dry scfm 588,655.4 614,144.0 614,660.3 605,819.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 838,159.2 874,633.2 878,556.3 863,782.900

Percent Isokinetic of Sampling Rate, % 98.3 95.7 95.6 96.533

F-Factor, dscfm/MMBtu @ %O2 9721 9718 9896 9,778.333

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 12 of 35
JEA, Northside Station, Unit 1

Emissions Summary

Location: Unit 1 Stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 1.47E-02 1.25E-02 1.38E-02 0.014

ppm 1.62E+01 1.43E+01 1.57E+01 15.400

ppm@7%O2 1.37E+01 1.15E+01 1.27E+01 12.633

Location: Unit 1 Stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000046 0.0000000051 0.0000000038 0.000

lb/mmBtuO2 4.02E-13 4.58E-13 3.51E-13 0.000

ng/dscm 5.23E-04 5.77E-04 4.34E-04 0.001

ng/dscm@7%O2 4.38E-04 4.92E-04 3.75E-04 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000034 0.0000000022 0.000

lb/mmBtuO2 2.80E-13 3.05E-13 2.03E-13 0.000

ng/dscm 3.64E-04 3.85E-04 2.51E-04 0.000

ng/dscm@7%O2 3.05E-04 3.28E-04 2.17E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000041 0.000000045 0.000000029 0.000

lb/mmBtuO2 3.59E-12 4.04E-12 2.68E-12 0.000

ng/dscm 4.66E-03 5.09E-03 3.31E-03 0.004

ng/dscm@7%O2 3.90E-03 4.34E-03 2.86E-03 0.004

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000034 0.000000004 0.0000000028 0.000

lb/mmBtuO2 2.97E-13 3.59E-13 2.58E-13 0.000

ng/dscm 3.86E-04 4.53E-04 3.20E-04 0.000

ng/dscm@7%O2 3.23E-04 3.86E-04 2.76E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000025 0.0000000018 0.000

lb/mmBtuO2 2.01E-13 2.24E-13 1.66E-13 0.000

ng/dscm 2.61E-04 2.83E-04 2.05E-04 0.000

ng/dscm@7%O2 2.19E-04 2.41E-04 1.77E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

Friday, February 04, 2011 Page 13 of 35
JEA, Northside Station, Unit 1

RunNumber 1 2 3

Mass_mg 0.0000000033 0.0000000038 0.0000000027 0.000

lb/mmBtuO2 2.89E-13 3.41E-13 2.49E-13 0.000

ng/dscm 3.75E-04 4.30E-04 3.08E-04 0.000

ng/dscm@7%O2 3.14E-04 3.67E-04 2.66E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000021 0.0000000022 0.0000000016 0.000

lb/mmBtuO2 1.84E-13 1.98E-13 1.48E-13 0.000

ng/dscm 2.39E-04 2.49E-04 1.83E-04 0.000

ng/dscm@7%O2 2.00E-04 2.12E-04 1.58E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000034 0.0000000039 0.0000000028 0.000

lb/mmBtuO2 2.97E-13 3.50E-13 2.58E-13 0.000

ng/dscm 3.86E-04 4.41E-04 3.20E-04 0.000

ng/dscm@7%O2 3.23E-04 3.76E-04 2.76E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000025 0.0000000027 0.000000002 0.000

lb/mmBtuO2 2.19E-13 2.42E-13 1.85E-13 0.000

ng/dscm 2.84E-04 3.06E-04 2.28E-04 0.000

ng/dscm@7%O2 2.38E-04 2.61E-04 1.97E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000041 0.0000000041 0.000000003 0.000

lb/mmBtuO2 3.59E-13 3.68E-13 2.77E-13 0.000

ng/dscm 4.66E-04 4.64E-04 3.42E-04 0.000

ng/dscm@7%O2 3.90E-04 3.96E-04 2.95E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000031 0.000000035 0.000000028 0.000

lb/mmBtuO2 2.71E-12 3.14E-12 2.58E-12 0.000

ng/dscm 3.52E-03 3.96E-03 3.20E-03 0.004

ng/dscm@7%O2 2.95E-03 3.38E-03 2.76E-03 0.003

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000091 0.0000000096 0.0000000111 0.000

lb/mmBtuO2 7.96E-13 8.62E-13 1.02E-12 0.000

ng/dscm 1.03E-03 1.09E-03 1.27E-03 0.001

ng/dscm@7%O2 8.62E-04 9.30E-04 1.10E-03 0.001

Friday, February 04, 2011 Page 14 of 35
JEA, Northside Station, Unit 1

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000000734 0.0000000222 0.00000005 0.000

lb/mmBtuO2 6.42E-12 1.99E-12 4.61E-12 0.000

ng/dscm 8.34E-03 2.51E-03 5.71E-03 0.006

ng/dscm@7%O2 6.98E-03 2.14E-03 4.93E-03 0.005

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000465 0.000000361 0.000000362 0.000

lb/mmBtuO2 4.07E-11 3.24E-11 3.34E-11 0.000

ng/dscm 5.28E-02 4.09E-02 4.13E-02 0.045

ng/dscm@7%O2 4.42E-02 3.49E-02 3.57E-02 0.038

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000274 0.0000000234 0.0000000167 0.000

lb/mmBtuO2 2.40E-12 2.10E-12 1.54E-12 0.000

ng/dscm 3.11E-03 2.65E-03 1.91E-03 0.003

ng/dscm@7%O2 2.60E-03 2.26E-03 1.65E-03 0.002

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000284 0.0000000109 0.0000000216 0.000

lb/mmBtuO2 2.48E-12 9.79E-13 1.99E-12 0.000

ng/dscm 3.23E-03 1.23E-03 2.47E-03 0.002

ng/dscm@7%O2 2.70E-03 1.05E-03 2.13E-03 0.002

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.000001351 0.000000898 0.00000125 0.000

lb/mmBtuO2 1.18E-10 8.06E-11 1.15E-10 0.000

ng/dscm 1.53E-01 1.02E-01 1.43E-01 0.133

ng/dscm@7%O2 1.28E-01 8.70E-02 1.23E-01 0.113

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000185 0.0000000119 0.000000015 0.000

lb/mmBtuO2 1.62E-12 1.07E-12 1.38E-12 0.000

ng/dscm 2.10E-03 1.35E-03 1.71E-03 0.002

ng/dscm@7%O2 1.76E-03 1.15E-03 1.48E-03 0.001

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.0000000024 0.0000000017 0.000

lb/mmBtuO2 1.92E-13 2.15E-13 1.57E-13 0.000

Friday, February 04, 2011 Page 15 of 35
JEA, Northside Station, Unit 1

ng/dscm 2.50E-04 2.72E-04 1.94E-04 0.000

ng/dscm@7%O2 2.09E-04 2.32E-04 1.67E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000036 0.0000000028 0.000

lb/mmBtuO2 2.80E-13 3.23E-13 2.58E-13 0.000

ng/dscm 3.64E-04 4.07E-04 3.20E-04 0.000

ng/dscm@7%O2 3.05E-04 3.47E-04 2.76E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000074 0.0000000089 0.0000000071 0.000

lb/mmBtuO2 6.47E-13 7.99E-13 6.55E-13 0.000

ng/dscm 8.41E-04 1.01E-03 8.11E-04 0.001

ng/dscm@7%O2 7.04E-04 8.61E-04 7.00E-04 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000005 0.0000000056 0.0000000043 0.000

lb/mmBtuO2 4.37E-13 5.03E-13 3.97E-13 0.000

ng/dscm 5.68E-04 6.34E-04 4.91E-04 0.001

ng/dscm@7%O2 4.76E-04 5.41E-04 4.24E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.000000058 0.00000003 0.0000000162 0.000

lb/mmBtuO2 5.07E-12 2.69E-12 1.49E-12 0.000

ng/dscm 6.59E-03 3.39E-03 1.85E-03 0.004

ng/dscm@7%O2 5.52E-03 2.89E-03 1.60E-03 0.003

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000263 0.0000000143 0.0000000167 0.000

lb/mmBtuO2 2.30E-12 1.28E-12 1.54E-12 0.000

ng/dscm 2.99E-03 1.62E-03 1.91E-03 0.002

ng/dscm@7%O2 2.50E-03 1.38E-03 1.65E-03 0.002

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000133 0.0000000239 0.000000095 0.000

lb/mmBtuO2 1.16E-12 2.15E-12 8.76E-12 0.000

ng/dscm 1.51E-03 2.70E-03 1.08E-02 0.005

ng/dscm@7%O2 1.26E-03 2.30E-03 9.32E-03 0.004

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Friday, February 04, 2011 Page 16 of 35
JEA, Northside Station, Unit 1

Mass_mg 0.0000000143 0.0000000109 0.000000017 0.000

lb/mmBtuO2 1.25E-12 9.79E-13 1.57E-12 0.000

ng/dscm 1.62E-03 1.23E-03 1.94E-03 0.002

ng/dscm@7%O2 1.36E-03 1.05E-03 1.67E-03 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000072 0.000000056 0.00000021 0.000

lb/mmBtuO2 6.30E-12 5.03E-12 1.94E-11 0.000

ng/dscm 8.18E-03 6.34E-03 2.40E-02 0.013

ng/dscm@7%O2 6.85E-03 5.41E-03 2.07E-02 0.011

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000038 0.00000006 0.000000039 0.000

lb/mmBtuO2 3.32E-12 5.39E-12 3.60E-12 0.000

ng/dscm 4.32E-03 6.79E-03 4.45E-03 0.005

ng/dscm@7%O2 3.62E-03 5.79E-03 3.84E-03 0.004

Compound: Total HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000046 0.000000051 0.000000038 0.000

lb/mmBtuO2 4.02E-12 4.58E-12 3.51E-12 0.000

ng/dscm 5.23E-03 5.77E-03 4.34E-03 0.005

ng/dscm@7%O2 4.38E-03 4.92E-03 3.75E-03 0.004

Compound: Total HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000036 0.000000039 0.000000025 0.000

lb/mmBtuO2 3.15E-12 3.50E-12 2.31E-12 0.000

ng/dscm 4.09E-03 4.41E-03 2.85E-03 0.004

ng/dscm@7%O2 3.42E-03 3.76E-03 2.46E-03 0.003

Compound: Total HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000063 0.000000059 0.000000039 0.000

lb/mmBtuO2 5.51E-12 5.30E-12 3.60E-12 0.000

ng/dscm 7.16E-03 6.68E-03 4.45E-03 0.006

ng/dscm@7%O2 6.00E-03 5.70E-03 3.84E-03 0.005

Compound: Total HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000023 0.000000024 0.000000018 0.000

lb/mmBtuO2 2.01E-12 2.15E-12 1.66E-12 0.000

ng/dscm 2.61E-03 2.72E-03 2.05E-03 0.002

ng/dscm@7%O2 2.19E-03 2.32E-03 1.77E-03 0.002

Friday, February 04, 2011 Page 17 of 35
JEA, Northside Station, Unit 1

Compound: Total PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000041 0.000000041 0.00000003 0.000

lb/mmBtuO2 3.59E-12 3.68E-12 2.77E-12 0.000

ng/dscm 4.66E-03 4.64E-03 3.42E-03 0.004

ng/dscm@7%O2 3.90E-03 3.96E-03 2.95E-03 0.004

Compound: Total PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000031 0.000000036 0.000000028 0.000

lb/mmBtuO2 2.71E-12 3.23E-12 2.58E-12 0.000

ng/dscm 3.52E-03 4.07E-03 3.20E-03 0.004

ng/dscm@7%O2 2.95E-03 3.47E-03 2.76E-03 0.003

Compound: Total TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000074 0.000000089 0.000000071 0.000

lb/mmBtuO2 6.47E-12 7.99E-12 6.55E-12 0.000

ng/dscm 8.41E-03 1.01E-02 8.11E-03 0.009

ng/dscm@7%O2 7.04E-03 8.61E-03 7.00E-03 0.008

Compound: Total TCDF 

Average

RunNumber 1 2 3

Mass_mg 0.00000005 0.000000056 0.000000043 0.000

lb/mmBtuO2 4.37E-12 5.03E-12 3.97E-12 0.000

ng/dscm 5.68E-03 6.34E-03 4.91E-03 0.006

ng/dscm@7%O2 4.76E-03 5.41E-03 4.24E-03 0.005

Location: Unit 1 Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 2.31E-03 1.33E-03 1.26E-03 0.002

ppm 1.61E+00 9.69E-01 9.11E-01 1.163

ppm@7%O2 1.36E+00 7.79E-01 7.36E-01 0.958

Location: Unit 1 Stack - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.53 3.45 0.55 1.510

lb/mmBtuO2 1.31E-04 8.64E-04 1.37E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.32 0.3 0.34 0.320

lb/mmBtuO2 7.90E-05 7.51E-05 8.44E-05 0.000

Friday, February 04, 2011 Page 18 of 35
JEA, Northside Station, Unit 1

Location: Unit 1 Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00645 0.00645 0.00575 0.006

lb/mmBtuO2 1.12E-06 1.10E-06 1.02E-06 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00233 0.00108 0.00068 0.001

lb/mmBtuO2 4.05E-07 1.84E-07 1.20E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00032 0.00032 0.00032 0.000

lb/mmBtuO2 5.56E-08 5.46E-08 5.65E-08 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.001064 0.001072 0.001063 0.001

lb/mmBtuO2 1.85E-07 1.83E-07 1.88E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00127 0.00099 0.00062 0.001

lb/mmBtuO2 2.21E-07 1.69E-07 1.09E-07 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.0048 0.001 0.001 0.002

lb/mmBtuO2 8.34E-07 1.71E-07 1.77E-07 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 5.55 3.15 3.15 3.950

lb/mmBtuO2 9.64E-04 5.37E-04 5.56E-04 0.001

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 2.0272 0.0156 0.3322 0.792

lb/mmBtuO2 3.52E-04 2.66E-06 5.86E-05 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.00135 0.00135 0.00043 0.001

Friday, February 04, 2011 Page 19 of 35
JEA, Northside Station, Unit 1

lb/mmBtuO2 2.34E-07 2.30E-07 7.59E-08 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.00184 0.00115 0.00088 0.001

lb/mmBtuO2 3.20E-07 1.96E-07 1.55E-07 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0029 0.00128 0.00102 0.002

lb/mmBtuO2 5.04E-07 2.18E-07 1.80E-07 0.000

Location: Unit 1 Stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 1.42E-01 1.51E-01 1.61E-01 0.151

ppm 6.76E+01 7.13E+01 7.62E+01 71.700

ppm@7%O2 5.73E+01 6.16E+01 6.58E+01 61.567

Location: Unit 1 Stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 8.82E-02 1.30E-01 9.43E-02 0.104

ppm 5.86E+01 8.53E+01 6.20E+01 68.633

ppm@7%O2 4.97E+01 7.36E+01 5.35E+01 58.933

Location: Unit 1 Stack - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 2.7 0.5 1 1.400

lb/mmBtuO2 6.13E-04 1.12E-04 2.26E-04 0.000

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 6.3 10.5 15 10.600

lb/mmBtuO2 1.43E-03 2.35E-03 3.40E-03 0.002

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 3.9 5.5 9.6 6.333

lb/mmBtuO2 8.86E-04 1.23E-03 2.17E-03 0.001

Compound: Total PM2.5

Average

RunNumber 1 2 3

Friday, February 04, 2011 Page 20 of 35
JEA, Northside Station, Unit 1

Process Run Data

Mass_mg 12.9 16.5 25.6 18.333

lb/mmBtuO2 2.93E-03 3.69E-03 5.79E-03 0.004

Friday, February 04, 2011 Page 21 of 35
JEA, Northside Station, Unit 1

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 3E+09 mmBtu/hr 3E+09

2 Heat Input 3E+09 mmBtu/hr 3E+09

3 Heat Input 3E+09 mmBtu/hr 3E+09

1 Gross Mwe 308 Mwe 300

2 Gross Mwe 308 Mwe 300

3 Gross Mwe 307 Mwe 300

1 Steam Flow 2066 k#/hr 2025

2 Steam Flow 2066 k#/hr 2025

3 Steam Flow 2059 k#/hr 2025

Run Name Value UOM Comments

Target

Value

1 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

0 0

1 DRY SCRUBBER 0 0

1 BAGHOUSE 0 0

Friday, February 04, 2011 Page 22 of 35
JEA, Northside Station, Unit 1

Sampling / Stack Data Results Detail

Location Unit 1 Stack - Method 10

Average

Run Number 1 2 3

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 AM 11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 AM 1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Fuel Factor 1.06 1.09 1.09

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9922 9921 9,887.667

Moisture, % 14.44 10.57 11.2 12.070

Analyzer Make Horiba Horiba Horiba

Analyzer Model VIA-510 VIA-510 VIA-510

Analyzer Serial Number 570124044 570124044 570124044 570,124,044

.000

Operating Range 15.9 15.9 15.9 15.900

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 17 18 18 17.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.28 0.15 0.19 0.207

Calibration Pre Zero Cylinder Bias -1.76 -1.89 -1.64 -1.763

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0005645 EB0005645 EB0005645

Calibration Pre High Cylinder Instrument Response 6.42 6.47 6.45 6.447

Calibration Pre High Cylinder Bias -2.89 1.07 0.94 -0.293

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.12 0.19 0.28 0.197

Calibration Post Zero Cylinder Bias -2.77 -1.64 -1.07 -1.827

Calibration Post Zero Cylinder Drift 1.01 0.25 0.57 0.610

Calibration Post High Cylinder ID EB0005645 EB0005645 EB0005645

Calibration Post High Cylinder Instrument Response 6.31 6.45 6.51 6.423

Calibration Post High Cylinder Bias -3.58 0.94 1.32 -0.440

Calibration Post High Cylinder Drift 0.69 0.13 0.38 0.400

Cavg 15.65 14.12 15.43 15.067

Cavg Units ppmvd ppmvd ppmvd

Cgas 16.1893 14.327 15.7181 15.411

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 23 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 23

Average

Run Number 1 2 3

Test Date 5/25/2010 5/26/2010 5/25/2010

Run Start Time 9:00:00 AM 11:50:00 AM 7:45:00 AM

Run Finish Time 5:15:00 PM 8:05:00 PM 3:56:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.185 0.185 0.185 0.185

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.009 1.009 1.009 1.009

Barometric Pressure, inches of Mercury 29.85 29.66 29.6 29.703

Average Orifice Meter Differential, inches H2O 1.35 1.38 1.36 1.363

Dry Gas Meter Volume Sampled, cubic feet 324.807 327.185 326.191 326.061

Average Dry Gas Meter Temperature, °F 97.13 95.52 97.58 96.743

Dry Gas Meter Volume Sampled, dscf 310.898 312.113 309.375 310.795

Total Moisture Liquid collected, g 805.6 750.7 734.2 763.500

Volume of Water Vapor, standard cubic feet 37.92 35.34 34.56 35.940

Moisture Content of Stack Gas, % 10.87 10.17 10.05 10.363

Moisture Saturation at Stack Gas Temperature, % 82.79 82.08 84.64 83.170

Dry Mole Fraction 0.8913 0.8983 0.8995 0.896

Carbon Dioxide, % 15.1 15.4 15.3 15.267

Oxygen, % 4.3 4.6 4.8 4.567

Carbon Monoxide & Nitrogen, % 80.6 80 79.9 80.167

Fuel Factor 1.10 1.06 1.05

Dry Molecular Weight, lb/lb-Mole 30.59 30.65 30.64 30.627

Wet Molecular weight, lb/lb-Mole 29.22 29.36 29.37 29.317

Flue Gas Static Pressure, inches of H2O -0.91 -0.94 -0.98 -0.943

Absolute Flue Gas Pressure, inches of Mercury 29.78 29.59 29.53 29.633

Average Stack Gas Temperature, °F 202.44 201.71 203.10 202.417

Average Velocity Head, inches of H2O 1.5413492193

9645

1.579161619

58504

1.545293630

16493

1.555

Average Stack Gas Velocity, feet/second 77.79 78.76 78.06 78.203

Stack Cross-Sectional Area, square feet 176.715 176.715 176.715 176.715

Dry Volumetric Flow Rate, dry scfm 583,207.1 591,972.3 585,074.4 586,751.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 824,799.6 835,084.4 827,662.4 829,182.133

Percent Isokinetic of Sampling Rate, % 105.1 104.0 104.3 104.467

Percent Excess Air, % 25.3 27.8 29.5 27.533

F-Factor, dscfm/MMBtu @ %O2 9796 9913 9973 9,894.000

Round Duct Diameter, inches 180 180 180

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 24 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 25A

Average

Run Number 1 2 3

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 AM 11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 AM 1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Fuel Factor 1.06 1.09 1.09

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9923 9923 9,888.667

Moisture, % 14.44 10.57 11.2 12.070

Analyzer Make Thermo Env. Thermo Env. Thermo Env.

Analyzer Model 51 51 51 51.000

Analyzer Serial Number 4723 4723 4723 4,723.000

Operating Range 9.03 9.03 9.03 9.030

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 19 20 20 19.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.15 0.12 0.2 0.157

Calibration Pre Zero Cylinder Bias 0.78 -0.33 0.55 0.333

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC243371 CC243371 CC243371

Calibration Pre High Cylinder Instrument Response 5.45 5.27 5.24 5.320

Calibration Pre High Cylinder Bias 2.21 1.33 1 1.513

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.11 0.2 0.27 0.193

Calibration Post Zero Cylinder Bias 0.33 0.55 1.33 0.737

Calibration Post Zero Cylinder Drift 0.45 0.88 0.78 0.703

Calibration Post High Cylinder ID CC243371 CC243371 CC243371

Calibration Post High Cylinder Instrument Response 5.31 5.24 5.29 5.280

Calibration Post High Cylinder Bias 0.66 1 1.55 1.070

Calibration Post High Cylinder Drift 1.55 0.33 0.55 0.810

Cavg 1.49 0.99 1 1.160

Cavg Units ppmvw ppmvw ppmvw

Cgas 1.6107 0.9691 0.9112 1.164

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 1.3781333333

3333

0.866653581

943081

0.809105367

79324

1.018

Cgasw Units ppmvw ppmvw ppmvw

Friday, February 04, 2011 Page 25 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 26A

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 AM 11:30:00 AM

Run Finish Time 5:50:30 PM 11:10:30 AM 2:42:30 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.185 0.185 0.185 0.185

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.014 1.01 1.01 1.011

Barometric Pressure, inches of Mercury 29.67 29.72 29.72 29.703

Average Orifice Meter Differential, inches H2O 1.43 1.39 1.47 1.430

Dry Gas Meter Volume Sampled, cubic feet 119.178 118.268 120.319 119.255

Average Dry Gas Meter Temperature, °F 103.83 100.25 104.83 102.970

Dry Gas Meter Volume Sampled, dscf 112.619 112.207 113.249 112.692

Total Moisture Liquid collected, g 274.7 216.1 256.2 249.000

Volume of Water Vapor, standard cubic feet 12.93 10.17 12.06 11.720

Moisture Content of Stack Gas, % 10.30 8.31 9.62 9.410

Moisture Saturation at Stack Gas Temperature, % 78.71 100.00 99.58 92.763

Dry Mole Fraction 0.897 0.9169 0.9038 0.906

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Carbon Monoxide & Nitrogen, % 80.3 80.1 80.1 80.167

Fuel Factor 1.08 1.07 1.07

Dry Molecular Weight, lb/lb-Mole 30.61 30.61 30.61 30.610

Wet Molecular weight, lb/lb-Mole 29.31 29.56 29.40 29.423

Flue Gas Static Pressure, inches of H2O -1.5 -1.5 -1.6 -1.533

Absolute Flue Gas Pressure, inches of Mercury 29.56 29.61 29.60 29.590

Average Stack Gas Temperature, °F 199.63 263.54 211.25 224.807

Average Velocity Head, inches of H2O 1.5384309385

6501

1.716074106

28702

1.646619322

1738

1.634

Average Stack Gas Velocity, feet/second 77.72 85.53 80.93 81.393

Stack Cross-Sectional Area, square feet 176.715 176.715 176.715 176.715

Dry Volumetric Flow Rate, dry scfm 584,556.2 600,500.4 603,512.5 596,189.700

Actual Wet Volumetric Flue Gas Flow Rate, acfm 824,057.4 906,866.0 858,092.7 863,005.367

Percent Isokinetic of Sampling Rate, % 101.3 98.3 98.7 99.433

Percent Excess Air, % 26.9 29.4 29.4 28.567

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Round Duct Diameter, inches 180 180 180

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 26 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 29

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 12:41:00 PM 7:27:00 PM 1:34:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.191 0.191 0.191 0.191

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.01 1.01 1.01 1.010

Barometric Pressure, inches of Mercury 29.75 29.75 29.67 29.723

Average Orifice Meter Differential, inches H2O 1.52 1.66 1.55 1.577

Dry Gas Meter Volume Sampled, cubic feet 166.515 172.266 168.358 169.046

Average Dry Gas Meter Temperature, °F 94.73 102.54 100.52 99.263

Dry Gas Meter Volume Sampled, dscf 159.765 163.044 159.448 160.752

Total Moisture Liquid collected, g 419.3 421.7 408.1 416.367

Volume of Water Vapor, standard cubic feet 19.74 19.85 19.21 19.600

Moisture Content of Stack Gas, % 11.00 10.85 10.75 10.867

Moisture Saturation at Stack Gas Temperature, % 75.68 74.43 77.35 75.820

Dry Mole Fraction 0.89 0.8915 0.8925 0.891

Carbon Dioxide, % 15.6 15.2 15.2 15.333

Oxygen, % 4.8 4.8 4.7 4.767

Carbon Monoxide & Nitrogen, % 79.6 80 80.1 79.900

Fuel Factor 1.03 1.06 1.07

Dry Molecular Weight, lb/lb-Mole 30.69 30.62 30.62 30.643

Wet Molecular weight, lb/lb-Mole 29.29 29.25 29.26 29.267

Flue Gas Static Pressure, inches of H2O -2.7 -1.4 -1.3 -1.800

Absolute Flue Gas Pressure, inches of Mercury 29.55 29.65 29.57 29.590

Average Stack Gas Temperature, °F 197.73 197.10 198.81 197.880

Average Velocity Head, inches of H2O 1.5278815235

9185

1.621320302

56723

1.527551735

63876

1.559

Average Stack Gas Velocity, feet/second 77.38 79.59 77.45 78.140

Stack Cross-Sectional Area, square feet 176.715 176.715 176.715 176.715

Dry Volumetric Flow Rate, dry scfm 578,929.3 599,059.7 580,520.8 586,169.933

Actual Wet Volumetric Flue Gas Flow Rate, acfm 820,452.4 843,884.8 821,194.6 828,510.600

Percent Isokinetic of Sampling Rate, % 102.1 100.7 101.6 101.467

Percent Excess Air, % 29.6 29.4 28.6 29.200

F-Factor, dscfm/MMBtu @ %O2 9695 9717 9896 9,769.333

Round Duct Diameter, inches 180 180 180

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 27 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A CO2

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 AM 11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 AM 2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Fuel Factor 1.08 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 651252 654698 603555 636,501.667

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Analyzer Make Calif. 

Analytical

Calif. 

Analytical

Calif. 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18 18 18 18.000

Operating Units % % %

No. Readings/Avg. 180 180 180 180.000

Calibration Set 5 6 6 5.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.11 0.15 0.15 0.137

Calibration Pre Zero Cylinder Bias 0.06 0 0 0.020

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275906_C CC275906_

C

CC275906_C

Calibration Pre High Cylinder Instrument Response 9.11 9.06 8.91 9.027

Calibration Pre High Cylinder Bias -0.22 0.22 -0.61 -0.203

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.12 0.15 0.1 0.123

Calibration Post Zero Cylinder Bias 0.11 0 -0.28 -0.057

Calibration Post Zero Cylinder Drift 0.05 0 0.28 0.110

Calibration Post High Cylinder ID CC275906_C CC275906_

C

CC275906_C

Calibration Post High Cylinder Instrument Response 8.95 8.91 9.03 8.963

Calibration Post High Cylinder Bias -1.11 -0.61 0.06 -0.553

Calibration Post High Cylinder Drift 0.89 0.83 0.67 0.797

Cavg 15.2 14.97 14.94 15.037

Cavg Units ppmvd ppmvd ppmvd

Cgas 15.2457 15.1135 15.0914 15.150

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 28 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A CO2 3

Average

Run Number 4 5 6

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 2:43:00 PM 9:25:00 PM 3:30:00 PM

Carbon Dioxide, % 15.6 15.2 15.2 15.333

Oxygen, % 4.8 4.8 4.7 4.767

Fuel Factor 1.03 1.06 1.07

Dry Volumetric Flow Rate, dry scfm 666360 689792 692409 682,853.667

F-Factor, dscfm/MMBtu @ %O2 9695 9717 9896 9,769.333

Moisture, % 11.61 11 11.19 11.267

Analyzer Make Calif. 

Analytical

Calif. 

Analytical

Calif. 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18 18 18 18.000

Operating Units % % %

No. Readings/Avg. 360 360 360 360.000

Calibration Set 9 9 10 9.333

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.12 0.13 0.11 0.120

Calibration Pre Zero Cylinder Bias 0.11 0.17 -0.22 0.020

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275906_C CC275906_

C

CC275906_C

Calibration Pre High Cylinder Instrument Response 9.02 9.23 9.11 9.120

Calibration Pre High Cylinder Bias -0.72 0.44 0.5 0.073

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.13 0.1 0.12 0.117

Calibration Post Zero Cylinder Bias 0.17 0 -0.17 0.000

Calibration Post Zero Cylinder Drift 0.06 0.17 0.05 0.093

Calibration Post High Cylinder ID CC275906_C CC275906_

C

CC275906_C

Calibration Post High Cylinder Instrument Response 9.23 9.29 8.95 9.157

Calibration Post High Cylinder Bias 0.44 0.78 -0.39 0.277

Calibration Post High Cylinder Drift 1.16 0.34 0.89 0.797

Cavg 15.68 15.59 15.17 15.480

Cavg Units ppmvd ppmvd ppmvd

Cgas 15.5723 15.2466 15.2154 15.345

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 29 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A CO2 3 6

Average

Run Number 7 8 9

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 AM 11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 AM 1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Fuel Factor 1.06 1.09 1.09

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9922 9921 9,887.667

Moisture, % 14.44 10.57 11.2 12.070

Analyzer Make Calif. 

Analytical

Calif. 

Analytical

Calif. 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18 18 18 18.000

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 13 14 14 13.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.1 0.15 0.08 0.110

Calibration Pre Zero Cylinder Bias -0.39 -0.17 -0.56 -0.373

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275906_C CC275906_

C

CC275906_C

Calibration Pre High Cylinder Instrument Response 8.99 8.89 8.91 8.930

Calibration Pre High Cylinder Bias 0.22 -1 -0.89 -0.557

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.17 0.08 0.22 0.157

Calibration Post Zero Cylinder Bias 0 -0.56 0.22 -0.113

Calibration Post Zero Cylinder Drift 0.39 0.39 0.78 0.520

Calibration Post High Cylinder ID CC275906_C CC275906_

C

CC275906_C

Calibration Post High Cylinder Instrument Response 8.97 8.91 8.88 8.920

Calibration Post High Cylinder Bias 0.11 -0.89 -1.06 -0.613

Calibration Post High Cylinder Drift 0.11 0.11 0.17 0.130

Cavg 15.21 15.56 15.46 15.410

Cavg Units ppmvd ppmvd ppmvd

Cgas 15.3562 15.8406 15.7739 15.657

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 30 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A O2

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 AM 11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 AM 2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Fuel Factor 1.08 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 651252 654698 667844 657,931.333

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Analyzer Make Calif. 

Analytical

Calif. 

Analytical

Calif. 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 180 180 180 180.000

Calibration Set 7 8 8 7.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.18 0.12 0.18 0.160

Calibration Pre Zero Cylinder Bias 0.22 -0.13 0.13 0.073

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275906 CC275906 CC275906

Calibration Pre High Cylinder Instrument Response 11.05 10.95 10.91 10.970

Calibration Pre High Cylinder Bias 0.54 -0.13 -0.31 0.033

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.1 0.18 0.1 0.127

Calibration Post Zero Cylinder Bias -0.13 0.13 -0.22 -0.073

Calibration Post Zero Cylinder Drift 0.35 0.26 0.35 0.320

Calibration Post High Cylinder ID CC275906 CC275906 CC275906

Calibration Post High Cylinder Instrument Response 11.11 10.91 10.99 11.003

Calibration Post High Cylinder Bias 0.8 -0.31 0.04 0.177

Calibration Post High Cylinder Drift 0.26 0.18 0.35 0.263

Cavg 4.6 4.81 4.87 4.760

Cavg Units ppmvd ppmvd ppmvd

Cgas 4.4845 4.7551 4.8131 4.684

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 31 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A O2 3

Average

Run Number 4 5 6

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 2:43:00 PM 9:25:00 PM 3:30:00 PM

Carbon Dioxide, % 15.6 15.2 15.6 15.467

Oxygen, % 4.8 4.8 4.8 4.800

Fuel Factor 1.03 1.06 1.03

Dry Volumetric Flow Rate, dry scfm 666360 689792 666360 674,170.667

F-Factor, dscfm/MMBtu @ %O2 9695 9717 9896 9,769.333

Moisture, % 11.61 11 11.61 11.407

Analyzer Make Calif. 

Analytical

Calif. 

Analytical

Calif. 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 360 360 360 360.000

Calibration Set 11 11 12 11.333

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.15 0.11 0.18 0.147

Calibration Pre Zero Cylinder Bias -0.13 -0.31 0.36 -0.027

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275906 CC275906 CC275906

Calibration Pre High Cylinder Instrument Response 10.95 10.93 11.05 10.977

Calibration Pre High Cylinder Bias -0.63 -0.71 0.13 -0.403

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.11 0.13 0.1 0.113

Calibration Post Zero Cylinder Bias -0.31 -0.22 0 -0.177

Calibration Post Zero Cylinder Drift 0.18 0.09 0.36 0.210

Calibration Post High Cylinder ID CC275906 CC275906 CC275906

Calibration Post High Cylinder Instrument Response 10.93 10.97 11.11 11.003

Calibration Post High Cylinder Bias -0.71 -0.54 0.4 -0.283

Calibration Post High Cylinder Drift 0.08 0.17 0.27 0.173

Cavg 4.82 4.88 4.83 4.843

Cavg Units ppmvd ppmvd ppmvd

Cgas 4.7724 4.8347 4.7157 4.774

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 32 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 3A O2 3 6

Average

Run Number 7 8 9

Test Date 5/20/2010 5/21/2010 5/21/2010

Run Start Time 3:15:00 PM 8:10:00 AM 11:15:00 AM

Run Finish Time 5:23:00 PM 10:20:00 AM 1:22:00 PM

Carbon Dioxide, % 15.4 15.8 15.8 15.667

Oxygen, % 4.5 3.6 3.7 3.933

Fuel Factor 1.06 1.09 1.09

Dry Volumetric Flow Rate, dry scfm 661068 645352 639766 648,728.667

F-Factor, dscfm/MMBtu @ %O2 9820 9922 9921 9,887.667

Moisture, % 14.44 10.57 11.2 12.070

Analyzer Make Calif. 

Analytical

Calif. 

Analytical

Calif. 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 15 16 16 15.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.11 0.2 0.18 0.163

Calibration Pre Zero Cylinder Bias -0.31 0.04 -0.04 -0.103

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275906 CC275906 CC275906

Calibration Pre High Cylinder Instrument Response 11.04 11.13 11.19 11.120

Calibration Pre High Cylinder Bias -0.04 0.04 0.31 0.103

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.15 0.18 0.25 0.193

Calibration Post Zero Cylinder Bias -0.13 -0.04 0.27 0.033

Calibration Post Zero Cylinder Drift 0.18 0.08 0.31 0.190

Calibration Post High Cylinder ID CC275906 CC275906 CC275906

Calibration Post High Cylinder Instrument Response 11.09 11.19 11.1 11.127

Calibration Post High Cylinder Bias 0.18 0.31 -0.09 0.133

Calibration Post High Cylinder Drift 0.22 0.27 0.4 0.297

Cavg 4.56 3.75 3.91 4.073

Cavg Units ppmvd ppmvd ppmvd

Cgas 4.4563 3.5697 3.7187 3.915

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 33 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 6C

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 AM 11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 AM 2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Fuel Factor 1.08 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 651252 654698 667844 657,931.333

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Analyzer Make Western 

Research

Western 

Research

Western 

Research

Analyzer Model 721M 721M 721M

Analyzer Serial Number 93-721M8062-693-721M8062-693-721M8062-6

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 180 180 180 180.000

Calibration Set 3 4 4 3.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.55 0.31 0.3 0.387

Calibration Pre Zero Cylinder Bias -0.14 -0.44 -0.45 -0.343

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0002329 EB0002329 EB0002329

Calibration Pre High Cylinder Instrument Response 50.54 50.69 50.99 50.740

Calibration Pre High Cylinder Bias -0.45 0.48 0.78 0.270

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.42 0.3 0.59 0.437

Calibration Post Zero Cylinder Bias -0.27 -0.45 -0.16 -0.293

Calibration Post Zero Cylinder Drift 0.13 0.01 0.29 0.143

Calibration Post High Cylinder ID EB0002329 EB0002329 EB0002329

Calibration Post High Cylinder Instrument Response 50.69 50.99 50.21 50.630

Calibration Post High Cylinder Bias -0.3 0.78 0 0.160

Calibration Post High Cylinder Drift 0.15 0.3 0 0.150

Cavg 67.31 71.37 75.81 71.497

Cavg Units ppmvd ppmvd ppmvd

Cgas 67.5848 71.297 76.1839 71.689

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 34 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - Method 7E

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/20/2010

Run Start Time 2:40:00 PM 8:00:00 AM 11:30:00 AM

Run Finish Time 6:13:00 PM 11:10:00 AM 2:42:00 PM

Carbon Dioxide, % 15.2 15.1 15.1 15.133

Oxygen, % 4.5 4.8 4.8 4.700

Fuel Factor 1.08 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 651252 654698 667844 657,931.333

F-Factor, dscfm/MMBtu @ %O2 9896 9821 9821 9,846.000

Moisture, % 10.3 8.31 9.63 9.413

Analyzer Make Thermo Env. Thermo Env. Thermo Env.

Analyzer Model 42C 42C 42C

Analyzer Serial Number 42CHL_67507

_357

42CHL_675

07_357

42CHL_6750

7_357

Operating Range 125 125 125 125.000

Operating Units ppm ppm ppm

No. Readings/Avg. 180 180 180 180.000

Calibration Set 1 2 2 1.667

Calibration Pre Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Pre Zero Cylinder Instrument Response 0.42 0.62 0.58 0.540

Calibration Pre Zero Cylinder Bias -0.1 -0.01 -0.04 -0.050

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC308924 CC308924 CC308924

Calibration Pre High Cylinder Instrument Response 50.49 50.41 50.23 50.377

Calibration Pre High Cylinder Bias 0.06 0.06 -0.08 0.013

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020795 EB0020795 EB0020795

Calibration Post Zero Cylinder Instrument Response 0.33 0.58 0.35 0.420

Calibration Post Zero Cylinder Bias -0.17 -0.04 -0.22 -0.143

Calibration Post Zero Cylinder Drift 0.07 0.03 0.18 0.093

Calibration Post High Cylinder ID CC308924 CC308924 CC308924

Calibration Post High Cylinder Instrument Response 50.59 50.23 50.58 50.467

Calibration Post High Cylinder Bias 0.14 -0.08 0.2 0.087

Calibration Post High Cylinder Drift 0.08 0.14 0.28 0.167

Cavg 58.48 84.38 61.61 68.157

Cavg Units ppmvd ppmvd ppmvd

Cgas 58.6089 85.2628 61.9531 68.608

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 35 of 35
JEA, Northside Station, Unit 1

Location Unit 1 Stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/18/2010 5/18/2010 5/19/2010

Run Start Time 8:30:00 AM 3:15:00 PM 9:25:00 AM

Run Finish Time 2:43:42 PM 8:25:48 PM 3:30:36 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 360 360 360

Nozzle Diameter, inches 0.138 0.138 0.138 0.138

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.014 1.014 1.014 1.014

Barometric Pressure, inches of Mercury 29.75 29.75 29.67 29.723

Average Orifice Meter Differential, inches H2O 0.23 0.23 0.23 0.230

Dry Gas Meter Volume Sampled, cubic feet 127.486 130.640 130.039 129.388

Average Dry Gas Meter Temperature, °F 94.33 99.75 95.50 96.527

Dry Gas Meter Volume Sampled, dscf 122.501 124.316 124.355 123.724

Total Moisture Liquid collected, g 342 326.4 332.5 333.633

Volume of Water Vapor, standard cubic feet 16.10 15.36 15.65 15.703

Moisture Content of Stack Gas, % 11.62 11.00 11.18 11.267

Moisture Saturation at Stack Gas Temperature, % 74.92 83.75 83.09 80.587

Dry Mole Fraction 0.8838 0.89 0.8882 0.887

Carbon Dioxide, % 15.6 15.2 15.2 15.333

Oxygen, % 4.8 4.8 4.7 4.767

Carbon Monoxide & Nitrogen, % 79.6 80 80.1 79.900

Fuel Factor 1.03 1.06 1.07

Dry Molecular Weight, lb/lb-Mole 30.69 30.62 30.62 30.643

Wet Molecular weight, lb/lb-Mole 29.22 29.23 29.21 29.220

Flue Gas Static Pressure, inches of H2O -2.1 -1.6 -1.5 -1.733

Absolute Flue Gas Pressure, inches of Mercury 29.60 29.63 29.56 29.597

Average Stack Gas Temperature, °F 197.33 202.75 202.25 200.777

Average Velocity Head, inches of H2O 1.5943218240

0605

1.724421525

72369

1.735888631

07348

1.685

Average Stack Gas Velocity, feet/second 79.05 82.49 82.86 81.467

Stack Cross-Sectional Area, square feet 176.715 176.715 176.715 176.715

Dry Volumetric Flow Rate, dry scfm 588,655.4 614,144.0 614,660.3 605,819.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 838,159.2 874,633.2 878,556.3 863,782.900

Percent Isokinetic of Sampling Rate, % 98.3 95.7 95.6 96.533

Percent Excess Air, % 29.6 29.4 28.6 29.200

F-Factor, dscfm/MMBtu @ %O2 9721 9718 9896 9,778.333

Round Duct Diameter, inches 180 180 180

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, February 04, 2011 Page 36 of 35