Date:  April 2010

To: Jim Eddinger, US EPA

From: Amanda Singleton, ERG

Subject:   MACT Floor Analysis (2010) for the Industrial, Commercial, and Institutional Boilers and

Process Heaters National Emission Standards for Hazardous Air Pollutants – Major Source

The purpose of this memorandum is to present the methodology and results of the maximum

achievable control technology (MACT) floor determinations for boilers and process heaters at major

sources of hazardous air pollutants (HAP). We determined the MACT floors using data obtained from

two recently implemented Information Collection Requests (ICRs) approved under OMB Control No.

2060‐0616: ICR numbers 2286.01 and 2286.03.1,2 Data from both phases—the 2008 Combustion Survey

and the 2009 Test Plan for boilers and process heaters—were analyzed for currently operating boilers

and process heaters. We ranked emission test averages for each boiler and process heater, calculated

MACT floor averages, and conducted emission data variability analyses. We determined the MACT floor

emission limits based on the results of these analyses. The following sections address the methodology

used to calculate pollutant limits for existing and new sources. The memorandum is organized as

follows:

1.0 Background of MACT Floor Methodology

2.0 Floors for Existing Sources

2.1 Methodology for MACT Floors for Existing Sources

2.2 Incorporating Data Variability

2.3 Calculating Emission Limits

2.4 Data Not Considered in the MACT Floor Analysis for Existing Units

3.0 Floors for New Sources

3.1 Methodology for MACT Floors for New Sources

4.0 Calculating Floors for the Alternative Solid Waste Definition

5.0 Calculating Floors with a Minimum of Five Test Results

Appendix A: Hg and HCl Variability as a Function of Fuel Variability

Appendix B: CO Variability as a Function of Boiler Load

Appendix C: Ranked Emission Data for MACT Floor Analysis

Appendix D: Upper Prediction Limit (UPL) Calculations for Existing Sources

Appendix E: Data Excluded from the Analysis for Existing Sources

Appendix F: UPL Calculations for New Sources

Appendix G: Ranked Emission Data and UPL Calculations for Existing Sources According to the

Alternative Non‐Hazardous Solid Waste Definition

0226.04.020 1
1.0 Background of MACT Floor Methodology

Section 112 of the Clean Air Act (CAA), as amended in November 1990, requires the U.S.

Environmental Protection Agency (EPA) to set emission standards for HAP emitted by major stationary

sources based on the performance of the MACT. Pollutants emitted by boilers and process heaters

include particulate matter (PM); mercury (Hg); non‐mercury metallic HAP; halogenated compounds (HCl,

HF, and Cl2); and organic HAP, including volatile organic compounds, dioxin, and polycyclic organic

matter.

On September 13, 2004, under authority of section 112 of the CAA , EPA promulgated national

emission standards for hazardous air pollutants (NESHAP) for new and existing

industrial/commercial/institutional boilers and process heaters. On June 19, 2007 the United States

Court of Appeals for the District of Columbia Circuit (DC Circuit) vacated the NESHAP for

industrial/commercial/institutional boilers and process heaters. The vacature occurred simultaneously

with the vacature of the CISWI solid waste definition rule (see Natural Resources Defense Council v. EPA,

489 F. 3d 1250, 1257–61 [D.C. Cir. 2007]). In this decision, the court determined that any combustion

device firing “any” solid waste material is subject to Section 129 instead of Section 112. As a result, EPA

has categorized units as either waste burning units, or boilers and process heaters, consistent with the

EPA proposed definition for nonhazardous solid waste. The new MACT floor analyses do not consider

emissions from waste burning units in the ranking analysis. If boilers and process heaters were burning

small amounts of waste materials or had indicated that they would stop burning materials that were

considered to be solid wastes, it is possible that a unit firing waste materials is in the boiler inventory,

but any emission test data based on tests when the unit was firing any amount of waste materials was

not included in the analysis. In the Emission database, the table ‘Data: Emission Test’ and the field ‘Test

Burning Proposed Option Waste?‘ indicates whether or not the test is firing waste materials, as defined

under the proposed solid waste definition. In the ‘Data: Fuel Analysis’ table the field ‘Proposed Option

Waste?’ denotes if a certain fuel is covered by the proposed solid waste definition.3 As the definition of

solid waste changes, EPA will continue to adjust combustion unit classifications and the subsequent

MACT floor analysis until the solid waste definition discussed above is promulgated.  

The revised MACT floor analysis discussed in this memorandum factors in other recent court

decisions that impacted the MACT floor analysis methodology used in the 2004 vacated rule. The March

2007 court decision (Sierra Club v. EPA, 479 F. 3d 875 [DC Cir. 2007]) (Brick MACT) found the following:

 Floors for existing sources must reflect the average emission limitation achieved by the best‐

performing 12 percent of existing sources, not levels EPA considers to be achievable by all

sources (479 F. 3d at 880–81).

 EPA cannot set floors of “no control.” The court reiterated its prior holdings, including National

Lime Association, confirming that EPA must set floor standards for all HAP emitted by the major

source, including those HAP that are not controlled by at‐the‐stack control devices (479 F. 3d at

883).

 EPA cannot ignore non‐technology factors that reduce HAP emissions. Specifically, the court

held that “EPA’s decision to base floors exclusively on technology even though non‐technology

factors affect emissions violates the Act” (479 F. 3d at 883).

 EPA may not use emission levels of the worst performers to estimate variability of the best

performers without a demonstrated relationship between the two (479 F. 3d at 882).

0226.04.020 2
2.0 Floors for Existing Sources

2.1 Methodology for MACT Floors for Existing Units

For existing sources, MACT cannot be less stringent than the average emission limitation

achieved by the best performing 12 percent of existing sources (for which emission information is

available) for categories and subcategories with 30 or more sources or the best performing five sources

for subcategories with less than 30 sources. The size of the subcategory was determined according to

the number of units in the boiler and process heater inventory, not the number of units within each

subcategory that had emission data available.

The new MACT floor analysis has the following differences from the analysis conducted for the

2004 vacated rule:

1) In response to the concern over MACT floor analyses based on control technologies, the

new approach ranks the performance of each pollutant according to the lowest emitting

(based on stack test data), regardless of control technologies installed on the boiler/process

heater.

2) Variability factors for Hg and chlorine (Cl) were assessed using fuel variability only from units

in the top 12 percent. Fuel variability was not used for units outside the top 12 percent.

3) Statistical variability was incorporated using the 99% Upper Prediction Limit (UPL).

4) Numerical limits were established for each HAP for each subcategory.

5) The number and type of subcategories were adjusted using unit design as the basis for the

subcategorization.  

Based on the 2008 Combustion Survey, there are 13,555 boilers/process heaters currently in

operation at major sources in the United States. Emission test data and additional Hg and Cl fuel analysis

data from uncontrolled liquid units were ranked and analyzed. These data were obtained from the

Boiler Survey, when available, or when requested under the ICR phase II testing plan, and compiled into

an emissions database.3 We used this database to develop the MACT floors.  

We identified the lowest emission test average (mean) for each pollutant at each boiler/process

heater. We did not include any data from units that indicated in their ICR responses that they were

permanently shut down. For units with a mix of detection levels and measures, we used the reported

numerical detection level. If a source reported “zero” or simply “ND” as the value for a test run, that run

was not used to calculate the average of the test. Similarly, if a unit reported data in the ICR that were

not standardized to the appropriate units of measure, or that did not provide operating and stack test

parameters necessary to standardize the emissions data, the data were not used in the MACT floor

analysis. For uncontrolled liquid units, we included reported fuel analysis data for Hg and Cl (converted

to HCl) in the ranking analysis for the MACT floors for units designed to burn liquid fuels. Details on how

these data were standardized are discussed in another memorandum.4

Next, we ranked the minimum stack test means for each pollutant in each subcategory. We

conducted this ranking according to the fuels the unit was designed to burn for Hg, PM, and HCl. For

0226.04.020 3
carbon monoxide (CO) and dioxin/furan, we conducted a ranking according to the combustor design

categories at solid fuel units, and according to the fuel the unit was designed to burn for liquid and

gaseous fuel units. Because emissions of fuel‐based HAP (e.g., Hg, acid gases, filterable particulate)

depend on the fuel used rather than the design of the combustion chamber, MACT floors for fuel‐based

HAP were based on data from all boilers and process heaters designed to burn the same type of fuel. For

boilers/process heaters burning multiple fuel types, we reviewed the emission database to determine

the relative heat input percentages each fuel category contributed during the test. If a test was fired

with at least 10 percent of the heat input from coal, the unit was classified as designed to burn coal. If

the test was fired with at least 10 percent biomass and less than 10 percent coal, the unit was classified

as designed to burn biomass. If the test was fired with at least 10 percent liquid and less than 10 percent

coal and less than 10 percent biomass, the unit was classified as designed to burn liquid. If a test was

fired with at least 10 percent of the heat input from a process gas (other than refinery gas) or some

other type of gas other than natural gas (e.g. landfill gas, digester gas), and less than 10 percent of the

heat input came from any solid or liquid fuel, the unit was classified as a unit designed to burn other

gases. If a unit fired refinery gas or natural gas, and less than 10 percent of the heat input came from

any other fuel, the unit was classified as designed to burn natural gas/refinery gas. Some units reported

test burns on more than one material. For example, units burning oil during periods of gas curtailment

might have submitted test results when firing natural gas and when firing fuel oil. The emission test data

based on fuel oil would have been characterized and ranked in the “boilers designed to burn liquids”

subcategory, but the emission test data based on natural gas would have been ranked and analyzed in

the “boilers designed to burn natural gas” subcategory.   

If an emission test result was conducted on a common stack, and the units feeding that stack

were boilers and process heaters in the same subcategory, each unit venting to a common stack was

treated as a separate data point. For example, if PM emissions were reported at a common stack for

boilers #1 and #2, we would have counted the results of those tests twice, to represent data from two

units. This approach avoids under estimating the number of sources for which data is available.

Emissions of organic HAP, including THC, CO, and dioxin/furans fluctuated according to the

design of the combustion chamber. Combustor design subcategories considered in this analysis were

Pulverized Coal (PC), Fluidized Bed (FB), and Stoker/Other for units designed to burn coal and

Stoker/Sloped Grate/Other, FB, Dutch Oven (including Suspension Burners), and Fuel Cells for units

designed to burn biomass. Because of these differences, MACT floors for dioxin/furans and CO were

based on unique combustor design characteristics in addition to the type of solid fuel the boiler is

designed to burn.  

We then identified minimum emission test averages in the best performing 12 percent (or top 5

units) for each subcategory. To determine the number of boilers/process heaters in the best‐performing

12 percent, we multiplied the number of sources with emission data in each subcategory by 12 percent

and rounded up to the nearest whole integer. For example, 12 percent of a category with 103 emission

test averages is 12.36, so we would have averaged the emission test data from the top 13

boilers/process heaters. This roundup approach is consistent with the approach used by statisticians in

survey sampling.5

0226.04.020 4
2.2 Incorporating Data Variability

Three types of data variability were evaluated to determine the emission levels achieved by the

best performing sources over the long term. This section discusses the statistical variability, fuel analysis

variability, and boiler operating load variability considered and incorporated into the MACT floor

analysis.

Statistical Variability6, 7

After identifying the units, based on minimum emission test averages, in the top 12 percent (or

top 5 units), we identified all the emission test runs reported for those top‐performing boilers/process

heaters to be in the same subcategory. By including multiple emission tests from units with a test

average in the top 12 percent, EPA can evaluate intra‐unit variability of emission tests over time,

considering variability in control device performance, unit operations, and fuels fired during the test. We

evaluated two statistical options based on statistical methods used in previous EPA rulemakings, the

99% upper limit and the 99% UPL.   

The Upper Limit (UL) is roughly equivalent to the 99th percentile of the actual data distribution

for the sample. While the UL has been utilized by EPA in some of its analyses (see Hospital, Medical,

Waste Incinerators rulemaking), it assumes that the data used represent the population rather than a

random sample from that population. The data used to calculate statistical variability on the MACT floor

analysis do not represent data from the entire population of affected boilers and process heaters in this

source category. Instead, EPA has collected a sample of emission data from random units in each

subcategory. Since the data used to calculate the MACT floor represents a sample of the population of

affected units, EPA determined that the upper limit was not an appropriate interval to use for assessing

variability.   

Instead, EPA selected the upper prediction limit (UPL). A prediction interval for a future

observation is an interval that will, with a specified degree of confidence, contain the next (or some

other pre‐specified) randomly selected observation from a population. In other words, the prediction

interval estimates what future values will be, based on present or past background samples taken. Given

this definition, the UPL represents the value we can expect the mean of three future observations

(three‐run average) to fall below, based on the results of the independent sample of size (n) from the

same population. In other words, if we were to randomly select a future test condition from any of

these sources (i.e., average of three runs), we can be 99 percent confident that the reported level will

fall below a MACT floor emission limit calculated using a UPL. Since a source must demonstrate

compliance with the MACT floor using the average of a three‐run test, the appropriate test

condition to use to assess variability is 3.  If a source had to demonstrate compliance by

showing that each individual test run was below the MACT floor emission limit, it would be

appropriate to use a future test condition of 1.

In light of comments made during the Hospital, Medical, Infectious Waste Incinerator

rulemaking, we first determined the distribution of the test run data for the best‐performing 12 percent

of units within each subcategory prior to calculating UPL values. To evaluate the distribution of the best

0226.04.020 5
performing dataset, we computed the skewness and kurtosis statistics and then conducted the

appropriate small‐sample hypothesis tests.

The skewness statistic (S) characterizes the degree of asymmetry of a given data distribution.

Normally distributed data have a skewness of 0. A skewness statistic that is greater (less) than 0

indicates that the data are asymmetrically distributed with a right (left) tail extending toward positive

(negative) values. Further, the standard error of the skewness statistic (SES) is given by SES = SQRT(6/N)

where N is the sample size. According to the small sample skewness hypothesis test, if the skewness

statistic (S) is greater than two times the SES, the data distribution can be considered non‐normal.  

The kurtosis statistic (K) characterizes the degree of peakedness or flatness of a given data

distribution in comparison to a normal distribution. Normally distributed data have a kurtosis of 0. A

kurtosis statistic that is greater (less) than 0 indicates a relatively peaked (flat) distribution. Further, the

standard error of the kurtosis statistic (SEK) is given by SEK = SQRT(24/N) where N is the sample size.

According to the small sample kurtosis hypothesis test, if K is greater than two times the SEK, the data

distribution is typically considered to be non‐normal.

We applied the skewness and kurtosis hypothesis tests to both the reported test values and the

lognormal values of the reported test values. If the S and K statistics of the reported dataset were both

less than twice the SES and SEK, respectively, the dataset was classified as normally distributed. If

neither of the S and K statistics or only one of these statistics was less than twice the SES or SEK,

respectively, then the skewness and kurtosis hypothesis tests were conducted for the natural log‐

transformed data. Then the distribution most similar to a normal distribution was selected as the basis

for calculating the UPL. If both the reported values and the natural‐log transformed reported values had

S and K statistics that were greater than twice the SES or SEK, respectively, the normally distributed

dataset was selected as the basis of the floor to be conservative. If the results of the skewness and

kurtosis hypothesis tests were mixed for the reported values and the natural log‐transformed reported

values, we also chose the normal distribution to be conservative. We believe this approach is more

accurate and obtained more representative results than a more simplistic normal distribution

assumption.

After determining the distribution of each dataset, a student’s t‐test statistic was used. The t‐

test was used in the promulgated HMWI rulemaking and proposed Portland Cement rulemaking, and it

is more appropriate for smaller sample sizes. The t‐statistic is calculated using the following Excel

equation:

t‐statistic = TINV(2*(1‐0.99),n‐1)

Where:

n = the number of test runs from units in the top 12 percent

Next, the average (or sample mean) and sample standard deviation of the test runs were calculated. We

calculated the 99% UPL values (which was determined to be the appropriate percentile to use in setting

MACT limits in the Hospital/Medical/Infectious Waste Incinerators NSPS) based on the test run data for

0226.04.020 6
those units in the best‐performing 12 percent. Since the compliance with the MACT floor emission limit

is based on the average of a three‐run test, the UPL is calculated by:

Where:

n = the number of test runs

m = the number of test runs in the compliance average

This calculation was performed using the following two Excel functions:

Normal distribution: 99% UPL = AVERAGE (Test Runs in Top 12%) + [STDEV(Test Runs in Top 12%) x

TINV(2 * 0.99, n‐1 degrees of freedom)*SQRT((1/n)+(1/3))], for a one‐tailed t‐value (with 2 x

probability), probability of 0.01, and sample size of n  

Lognormal distribution: 99% UPL = EXP{AVERAGE(Natural Log Values of Test Runs in Top 12%) +

[STDEV(Natural Log Values of Test Runs in Top 12%) x TINV(2 * 0.99, n‐1 degrees of freedom) *

SQRT((1/n)+(1/3))]}, for a one‐tailed t‐value (with 2 x probability), probability of 0.01, and sample size of

n

Fuel Analysis Variability

The UPL analysis discussed above takes into account intra‐unit variability within test runs, and

since the compliance date of the vacated boiler MACT was after the date the rule was vacated, often

there were only one or two tests available at a unit. These tests represent a small snapshot of the

overall unit operations, and based on the fuel analysis data reported in the Boiler Survey and the Phase

II test plan, fuel‐related HAP levels in the various fuels can vary significantly over time. These fuel‐

related HAP levels are not well‐represented in a small sample of emission stack test results.

Fuel analysis data for Hg and HCl (converted from Cl) were standardized to a lb/million Btu

(lb/mmBtu) basis, using data standardization techniques discussed in another memorandum.4 Next, the

units that reported fuel analysis data paired with stack tests were identified by using the database field

in the Data: Fuel Analysis table, “FM_analysiswithEmissionTest”. Since the Phase II test plan requested

paired fuel analysis data for each stack test run, the fuel analysis “Sample ID” associated with each fuel

analysis were matched up with the individual test run “Test ID.”  Since fuel sampling IDs reported in the

spreadsheet and test IDs reported in the Electronic Reporting tool sometimes had different naming

conventions, the IDs of the units in the top 12 percent were reviewed and a secondary test ID column

was created in order to allow these two data tables to be linked and compared.

Single‐Fuel Units

For boilers combusting a single fuel during a stack test, a control efficiency was calculated by

comparing the stack test result for Hg or HCl on each test run to the inlet HAP content from the fuel

0226.04.020 7
analysis corresponding to that test run. This control efficiency was calculated using the following

emission database fields and this Microsoft Access equation:

Control Efficiency =   

([Data: FuelAnalysis]![StdFuelBased EF (lbpermmBtu)]‐[Data: EmissionsTest]![Averaging Value])/

[Data: FuelAnalysis]![StdFuelBased EF (lbpermmBtu)

Next, the average (mean) of these calculated control efficiencies was calculated for each unit

with paired emission test and fuel analysis data. The average control efficiency was applied to all

standardized fuel analysis data reported for the boiler or process heater to calculate a control‐based

emission factor for the fuel HAP content for each reported analysis. The maximum fuel HAP content at

each unit, after applying the control efficiency, was divided by the average stack test result for that unit

to identify cases where fuel HAP content may exceed the results of a stack test.  

Multi‐Fuel Units

For boilers combusting multiple fuels during a test, the HAP content of each individual fuel

varies over time, and the relative heat input contribution of multiple fuel types can also vary over time.

To evaluate the impact of fuel variability at multi‐fuel boilers, the average reported fuel input rate,

standardized to mmBtu/hr, for each of the fuels fired during the test was calculated. Next the Hg or HCl

(converted from Cl) content of each fuel was multiplied by the fuel input rate to calculate an emission

rate from each fuel type, on a lb/hr basis. The fuel resulting in the highest Hg or HCl emissions, on a

lb/hr basis, was the predominant driver of Hg or HCl emissions, and its variability was used to evaluate

the variability in HAP content over subsequent fuel analyses of that fuel.  

After the predominant fuel for Hg and HCl was identified, the same control efficiency

calculations used to evaluate variability for single‐fuel units were applied. Then the maximum fuel HAP

content of the predominant fuel at each unit was divided by the average stack test result for that unit to

identify cases where fuel HAP content exceeded the results of a stack test.

Review of Outliers

The calculated variability factors for Hg and HCl were ranked in ascending order for each

subcategory (coal, biomass, and liquid), and the interquartile range (IQR) of the variability factors was

computed to identify any variability factors that might be outliers. No Hg or HCl fuel analysis variability

factors could be calculated for gas‐fired units. Variability factors outside of the IQR were not considered

in further analysis. Appendix A‐1 shows the IQR analysis for Hg and HCl.  

Developing a Fuel Variability Factor for Each Fuel Category

Because variability is considered only from units identified to be in the top 12 percent, the list of

fuel analysis data was limited to only those units that were in the top 12 percent for Hg or HCl. To

calculate the MACT floor emission limit for Hg and HCl, the 99% UPL emission limit was multiplied by the

average (mean) of all fuel variability factors for units in the top 12 percent of each fuel category.

0226.04.020 8
Appendix A‐2 shows the calculated fuel variability factors used in the MACT floor analyses for coal,

biomass, and liquid fuels.

Load Variability

For combustion‐based emissions, such as CO, formaldehyde, dioxin/furan, and total

hydrocarbons, the formation of emissions are dependent on the design of the combustion unit; the

MACT floor emission limits for CO and dioxin/furan are subcategorized according to combustor design

for boilers burning solid fuels. However, the emissions can fluctuate with changes in the operating rate

of a boiler, or “boiler load”. Boiler load was divided into two subcategories, depending on the role of a

boiler at a facility. A boiler providing a relatively constant amount of steam to a facility is considered a

“base‐loaded” unit, and a boiler that adjusts its operating parameters to meet varying levels of demand

in a plant over time is referred to a “load‐following” unit.  

Stack tests for CO are conducted at near full‐load conditions, and although the MACT floor limits

based on stack test results  achieved when operating at or near full load, the MACT floor emission levels

for CO might not be achieved when best performing units are operating at lower loads. For units greater

than 100 mmBtu/hr, the proposal required units to demonstrate compliance with emission limits by

using a CO continuous emissions monitoring system (CEMS) and calculating a 30‐day rolling average. The

Phase II ICR collected 30‐day monitoring data on an hourly average interval for CO, , and THC from six

different boilers. Two boilers fired coal, two fired biomass, and two fired gas (one refinery gas and one

natural gas). Each unit submitting 30‐day monitoring data also reported the boiler load during each

hourly average. These monitoring data were reviewed and standardized to a common basis, ppm @ 3%

O2. Then, each unit’s CO and THC data were plotted against the boiler load. Data corresponding to

malfunction in the CO, THC, or load monitor were removed from the dataset prior to plotting. The

graphs containing the CO emissions as a function of boiler load are shown in Appendix B.  

Each graph was reviewed to examine the variability of CO emissions as a function of boiler load.

The emissions included all periods of normal operation as well as start‐up and shutdown. No data

associated with periods of malfunction were included in the graphs. Based on the six graphs, only the

boilers firing biomass appear to show an inverse relationship between load and emissions. For these two

units firing biomass fuels (TXDibollTemple‐Inland, PB‐44; ARDomtarIndustries, PB1) there was a trend of

increased CO emissions at lower boiler loads. Of these two units, only the TXDibollTemple‐Inland, PB‐44

unit was in the top 12 percent for CO emissions at Dutch oven boilers. The 30‐day period reported by

TXDibollTemple‐Inland included boiler loads ranging from 17 to 77 percent of the rated design capacity

of unit PB‐44 and represents a boiler with large fluctuations in load.  The ARDomtarIndustries, PB1 boiler

is no longer in the boiler inventory, as it was identified as burning fuel cubes, a waste material under the

proposed solid waste definition rule; therefore, its data was not used to assess CO variability as a

function of boiler load.

A daily average was calculated for CO emissions from TXDibollTemple‐Inland unit PB‐44, based

on the hourly averages reported for the 30‐day CO and THC monitoring data. The result was 1,113 ppm

@ 3% O2.  This average is similar to the numerical limited calculated using 99% UPL for the dutch oven

0226.04.020 9
and suspension burner subcategory.  Therefore, we concluded that the statistical variability correctly

accounts for variability in CO emissions over various boiler loads.   

2.3 Calculating Emission Limits

We determined emission limits for each MACT floor option and pollutant by rounding up the

UPL values less than 100 to one significant figure, rounding the UPL values between 100 and 1,000 to

two significant figures, and rounding up the UPL values greater than or equal to 1,000 to three

significant figures. This approach allows for an appropriate level of precision depending on the scale of

the measured value. For example, we determined the MACT floor emission limit for Hg at coal

boilers/process heaters by rounding up the 99% UPL value after applying the fuel variability factor for Hg

(1.52E‐06 pounds per million Btu [lb/mmBtu]) to 2.64E‐06 lb/mmBtu. For CO emissions, calculated ppm

values less than 1 ppm were rounded up to 1 ppm, because measurement precision of CO emissions less

than 1 ppm were expected to be difficult for some sources. For CO emissions between 1 and 10 ppm,

the emissions were rounded up to the nearest whole integer. For CO emissions above 10 ppm, CO

emissions were rounded up to the nearest 10 ppm. It should be noted that if the UPL values were

rounded down, then the possibility exists that the best‐performing units comprising the MACT floor

might not be able to achieve the emission limit on an ongoing basis. In all cases, the significant figure

approach and associated rounding does not meaningfully change the emission limits. The emission limits

are summarized for each subcategory in Table 2. The data ranked and analyzed for the MACT floor at

existing units is shown in Appendix C, and the UPL floor calculations for each subcategory and each

pollutant are shown in Appendix D.  

Table 1: Summary of Calculated MACT Floor Limits for Existing Boilers and Process Heaters at Major Sources of HAP

 Subcategory 

PMFilterable 

(lb/mmBtu) 

Hg 

(lb/mmBtu) 

HCl 

(lb/mmBtu) 

CO 

(ppm @3% 

O2) 

TEQ 

dioxin/Furan

(ng/dscm 

@7% O2) 

Boilers and Process Heaters Designed to Burn Coal 2.00E-02 3.00E-06 2.00E-02 

Stoker/Sloped Grate/Other 50 3.00E-03 

FB 30 2.00E-03 

PC 90 4.00E-03 

Boilers and Process Heaters Designed to Burn 

Biomass 2.00E-02 9.00E-07 6.00E-03 

Stoker/Sloped Grate/Other 560 4.00E-03 

Fuel Cell 270 2.00E-02 

FB 250 2.00E-02 

Dutch Oven 1010 3.00E-02 

Boilers and Process Heaters Designed to Burn 

Liquids 4.00E-03 4.00E-06 9.00E-04 1 2.00E-03 

Boilers/PH Designed to Burn Natural Gas, Propane, 

LPG, Refinery Gas, Excluding Metallurgical Furnaces 3.00E-02 2.00E-07 2.00E-04 20 1.00E-02

Metallurgical Process Furnaces Designed to Burn 

Natural Gas 2.00E-02 2.00E-07 4.00E-04 2 4.00E-03

Boilers and Process Heaters Designed to Burn Other 

Gases 5.00E-02 2.00E-07 3.00E-06 1 9.00E-03 

Notes:

 Red text indicates at least one test run used to calculate the 99% UPL limit was reported as non‐detect data.  

 Blue shaded cells indicate limits that incorporate fuel analysis variability.

 Although floors were calculated, no numerical emission limits are proposed for new units firing natural gas/refinery gas.

2.4 Data Not Considered in the MACT Floor Analysis for Existing Units

0226.04.020 10
For fuel‐based HAP, data upstream of the control device were not considered in the MACT floor

analysis because the control device is expected to achieve emission reductions. The location of the test

is denoted in the “Location” field of the Data: Emission Test Table. If the test location was not reported,

it was assumed to be downstream of the control device. The upstream/downstream location was not a

limiting factor when identifying suitable data for CO, THC, and dioxin/furan, although in all cases, THC

and dioxin/furan emissions were downstream of the control device.

One unit reported emission data from test burns that did not fit into any of the five fuel

categories. MIVersoPaperQuinnesec reported a test burn on 100 percent tire‐derived fuel (TDF). This

does not reflect normal fuel blends at the boiler and was not included in the MACT floor analysis.  

Some facilities submitted emission test data based on previous control configurations that are

no longer installed on the unit. Emission data reported while using these previous control configurations

were not used to establish the MACT floor. Table 3 shows which control configurations were not

considered in the MACT floor analysis. Any emissions associated with the control configurations at these

units were not considered in the analysis, except the emissions for CO, as CO is not expected to be

affected by the control device installed on the unit.

Table 2: Deleted Control Configurations for MACT Floor Analysis

FacilityID UnitID DeleteRecord Reason for Removing

NCNC_DukeUniversity_Durham 7754-01 Fabric Filter Dry injection added to FF in 

2007

OHMedicalCenterCo1915 B003 & B004 Fabric Filter Dry injection added to FF in 

2007

MSMasoniteLaurel BB-003 Wet Scrubber Wet scrubber removed in 2007

MIMichiganSugarCaro Boilers #1 & #2 No HAP APCD 

Control

Venturi installed in 2007

ARGeorgiaPacificCrossett93 SN-WB1 Wood 

Boiler

Wet Scrubber Wet scrubber no longer 

installed at unit

SCNewSouthCamden WWB1 Cyclone or 

Multiclone

ESP installed in 2007

SCNewSouthCoConway WWB1 Cyclone or 

Multiclone

ESP installed in 2007

For uncontrolled light liquid units with fuel analysis data for Hg or HCl, the fuel analysis data

were only used if there was not an emission test available for that unit for Hg or HCl. Using both fuel

analysis and emission test data associated with the same unit would be double‐counting emission data

and would be inconsistent with the approach to use the minimum available emission data for each unit

to identify the units in the top 12 percent.

Some emission data for CO or dioxin/furan were based on common stacks that are fed from

units in more than one subcategory. Because the CO and dioxin/furan MACT floors are based on

combustor design, only those emissions are based on units of the same combustor. If the combustor

0226.04.020 11
design classification in the Data: Emission Test table listed “Multiple Combustor Designs,” this data was

not used in the MACT floor calculations for CO or dioxin/furan.

Finally, there were some specific data reported that were excluded from the MACT floor

analysis. PM data at WAGraysHarborPaper was reported using method OTM 27/OTM 28; however, the

unit has a wet scrubber installed, and this method is not applicable at wet stacks. WICharterSteel

reported total dioxin/furan data on a total mass basis; however, based on the large values of these data

compared to all other dioxin/furan data, they were identified as outliers and not included in the

analysis. The metals data (including mercury) reported for CTCytecWallingford were also identified as

outliers. These data were submitted in the Electronic Reporting Tool (ERT). Upon comparison to the

hard copy test report submitted with the ERT each individual metal was reported as non‐detect with a

lb/mmBtu value of zero in the hard copy of the test report.8 Since the ERT values were outliers and could

not be confirmed against the hard copy of the test report, the data was not used in the MACT floor

analysis. Appendix E lists the specific facility data not considered in the MACT floor analysis.

3.0 Floors for New Sources

3.1 Methodology for MACT Floor at New Units

The same methodology used to calculate the MACT floors for existing sources, as discussed in

Section 2.0, was used to calculate the floor for new sources, with three exceptions. First, if the

calculated floor for new sources was less stringent than the calculated floor for existing sources, the

floor corresponding to the same subcategory for existing sources was used as the basis for the floor for

new sources. Although the minimum average test run for the best performing source resulted in the

lowest three‐run average test, the 99% UPL‐based limit incorporated variability between test runs. As

the sample size—in this case the number of test runs—gets smaller, the t‐statistic increases. When the

sample size of test runs is small, and there is a large variability between test runs, the calculated limit

using the UPL approach can be larger than the variability among a larger set of test runs from units in

the best performing 12 percent, especially if the performance of the best performing units is

comparable. Similar to the approach used in the HMIWI rulemaking, if the emission limit for new

sources was less stringent than the emission limit for existing sources in the same subcategory, we

decided to use existing source limits for new sources.  

Second, if the lowest emitting unit had less than three test runs, the unit with the next lowest

emissions based on at least a three‐run test average was used as the basis for the MACT floor from new

units. Using the lowest emitting unit with three test runs ensures that adequate variability can be

incorporated into the limit to guarantee that future sources can repeatedly meet the limit during their

compliance tests. The next lowest unit was used in three instances:   

1) For the HCl MACT floor for new units designed to burn coal, the second lowest test

average was used because the lowest test average was based on only two test runs.

0226.04.020 12
2) For CO MACT floor for new units designed to burn natural gas/refinery gas, and

metallurgical furnaces designed to burn natural gas the second lowest test average was

used because the lowest test average was based on less than two runs.

3) For HCl emissions from new units designed to burn liquids, the two lowest emissions are

based on Cl content from reported fuel analysis data. The lowest emission test was from

a unit burning anhydrides residue, an on‐site process liquid. Since this liquid is specific to

a process and is not routinely available to other units in the category, it does not

represent the best performing similar source for other boilers designed to burn liquid

fuels. The floor was based on the second lowest three‐run test instead of the fuel

analysis data or the test based on anhydrides residue.

4) For dioxin/furan TEQ MACT floor for new units designed to burn liquids the second

lowest test was used since the top performing unit burns anhydrides residue, an on‐site

process liquid not representative of other units in the category.

Table 4 summarizes the MACT floor emission limits for new sources, and the light green

highlighted cells represent the limits where the corresponding limit for existing sources in the same

subcategory were used as a basis for the limit at new sources.  The UPL floor calculations for each

subcategory and each pollutant for new sources are shown in Appendix F.

To assess fuel variability, the same procedures were used; however, only fuel analysis variability

from the top‐performing unit in each subcategory was considered in the analysis. For load variability,

the PB‐44 boiler at TXTemple‐Inland Diboll was not the top‐performing Dutch oven boiler for CO

emissions, so its CO variability over various boiler loads was not considered in the calculated MACT floor

limit for new sources.  

0226.04.020 13
Table 1: Summary of MACT Floor Limits for New Boilers and Process Heaters at Major Sources of HAP

Subcategory PM- Filterable 

(lb/mmBtu) 

Hg 

(lb/mmBtu) 

HCl 

(lb/mmBtu) 

CO 

(ppm @3% O2) 

TEQ Dioxin/Furan

(ng/dscm @7% 

O2) 

Boilers and 

Process Heaters 

Designed to Burn 

Coal 1.00E-03 2.00E-06 6.00E-05 

Stoker/Sloped 

Grate/Other 7 3.00E-03 

Fluidized Bed 30 3.00E-05 

Pulverized Coal 90 2.00E-03 

Boilers and 

Process Heaters 

Designed to Burn 

Biomass 8.00E-03 2.00E-07 4.00E-03 

Stoker/Sloped 

Grate/Other 560 5.00E-05 

Fuel Cell 270 5.00E-04 

Fluidized Bed 40 7.00E-03 

Dutch Oven/Susp 

Burner 1,010 3.00E-02 

Boilers and 

Process Heaters 

Design to Burn 

Liquids 2.00E-03 3.00E-07 4.00E-04 1 2.00E-03

Boilers and 

Process Heaters 

Designed to Burn 

Natural Gas, 

Propane, LPG, 

Refinery Gas, 

Excluding 

Metallurgical 

Furnaces 5.00E-04 2.00E-07 2.00E-04 20 1.00E-02 

Metallurgical 

Process Furnaces 

Designed to Burn 

Natural Gas 2.00E-02 2.00E-07 2.00E-04 2 4.00E-03 

Boilers and 

Process Heaters 

Designed to Burn 

Other Gases 3.00E-03 2.00E-07 3.00E-06 1 9.00E-03 

Notes:

 Red text indicates at least one test run used to calculate the 99% UPL limit was reported as non‐detect data.  

 Blue shaded cells indicate limits that incorporate fuel analysis variability.

 Light green shaded cells indicate limits where the calculated limit for new sources was less stringent than the calculated limit for

existing sources, so the limit for existing sources was used as the basis for the limit at new sources.

 Although floors were calculated, no numerical emission limits are proposed for new units firing natural gas/refinery gas.

4.0 Calculating Floors for the Alternative Proposed Solid Waste Definition

Concurrent with this proposed rulemaking for boilers and process heaters, an alternative

definition of solid waste is being proposed by EPA’s Office of Resource Conservation and Recovery

(OCRC). An alternative MACT floor analysis was conducted, taking into account the materials classified

as solid wastes under the  proposed alternative solid waste definition. Boilers or process heaters firing

materials classified as wastes under the alternative approach were removed from the emission

inventory, as long as they fired those materials greater than 25 percent of the reported operating hours,

and those materials were not listed as “start‐up” only materials. If a unit was firing materials less than

0226.04.020 14
25 percent of the reported operating hours, or only listed waste materials during start‐up, EPA assumed

these units would stop burning wastes to avoid being classified as a CISWI unit. Considering the

alternative definition of solid waste, there are 13,275 boilers and process heaters estimated in operation

in the United States.  We analyzed emission test and fuel analysis data reported from these units for

calculating an alternative set of MACT floor numerical emission limits. For this alternative analysis

emission tests conducted while a unit was firing any amount of waste (as defined under the alternative

definition) were excluded from the MACT floor analysis.  In the Emission database, the table ‘Data:

Emission Test’ the  field ‘Alternative Waste Inventory?’ denotes whether the unit is covered under the

alternative solid waste definition and the field ‘Test Burning Alternative Option Waste?’ indicates

whether or not the test is firing waste materials, as defined under the alternative definition. In the

‘Data: Fuel Analysis’ table the field ‘Alternative Option Waste?’ denotes if a certain fuel is covered by the

alternative solid waste definition.

The data were ranked and analyzed using same methodology used to calculate the MACT floors

for existing sources, as discussed in Section 2.0. The calculated MACT floors under the alternative

approach are shown in Table 5. Details of the data used to rank and calculate the MACT floors under the

alternative approach are shown in Appendix G.

Table 2 Summary of MACT Floor Limits for Existing Boilers and Process Heaters at Major Sources of HAP, Considering the

Proposed Alternative Definition of Nonhazardous Solid Waste.

SUBCATEGORY 

PM- Filterable

(lb/mmBtu) 

Hg 

(lb/mmBtu) 

HCl 

(lb/mmBtu) 

CO 

(ppm @3% 

O2) 

TEQ 

Dioxin/Furan

(ng/dscm 

@7% O2) 

Boilers and Process Heaters Designed to 

Burn Coal 3.00E-02 4.00E-06 2.00E-02 

Stoker/Other 40 3.00E-03 

FB 50 8.00E-03 

PC 90 4.00E-03 

Boilers and Process Heaters Designed to 

Burn Biomass 2.00E-02 5.00E-07 3.00E-02 

Stoker/Other 180 5.00E-05 

Fuel Cell 460 2.00E-02 

FB 10650 1.00E-01 

Dutch Oven 1060 3.00E-01 

Boilers and Process Heaters Design to Burn 

Liquids 4.00E-03 5.00E-06 2.00E-03 1 2.00E-03 

Boilers and Process Heaters Designed to 

Burn Natural Gas, Propane, LPG, Refinery 

Gas, Excluding Metallurgical Furnaces 3.00E-02 2.00E-07 2.00E-04 20 1.00E-02

Metallurgical Furnaces (Process Heaters) 

Designed to Burn Natural Gas 2.00E-02 2.00E-07 4.00E-04 2 4.00E-03

Boilers and Process Heaters Designed to 

Burn Other Gases 5.00E-02 2.00E-07 3.00E-06 1 9.00E-03 

Notes:

 Red text indicates at least one test run used to calculate the 99% UPL limit was reported as non‐detect data.  

 Blue shaded cells indicate limits that incorporate fuel analysis variability.

 Although floors were calculated, no numerical emission limits are proposed for existing units firing natural gas/refinery gas.

0226.04.020 15
5.0 Calculating Floors with a Minimum of Five Test Results

The proposal is requesting comment on calculating MACT floors for source categories with more

than 30 affected sources on a minimum of five sources instead of using data from the top 12

percent of units with available data. Appendix H presents the UPL calculations considering a

minimum of five sources.  For dutch oven boilers, the dioxin TEQ floor is based on three data

points since no other data were available.

0226.04.020 16
0226.04.020 17

6.0 References

1. Phase I ICR 2008 Combustion Survey. [ICR No. 2286.01]. OMB Control No. 2060‐0616 ‐ Information

Collection Effort for Facilities with Combustion Units. Approved by OMB on August 1, 2008.

2. Phase II ICR Test Plan Requesting Emission Testing from Boilers, Process Heaters, and CISWI. [ICR No.

2286.03]. OMB Control No. 2060‐0616 ‐ Information Collection Effort for Facilities with Combustion

Units. Approved by OMB on May 21, 2009.

3. Emissions Database for Boilers and Process Heaters Containing Stack Test, CEM, & Fuel Analysis Data

Reported under ICR No. 2286.01  & ICR No. 2286.03 (version 5)

4. Gibson, G. and A. Singleton. ERG. 2010. Standardization of Reported Data from the Questionnaire for

Boilers, Process Heaters, Incinerators and Other Combustion Units.  

5. Cochran, William G. 1977. Sampling Techniques. Third Edition, John Wiley & Sons. Pages 72‐87.

6. Hahn GJ & Meeker WQ. 1991. Statistical Intervals: A Guide for Practitioners. John Wiley & Sons, Inc.:

New York.

7. NIST/SEMATECH. 2009. NIST/SEMATECH e‐Handbook of Statistical Methods,

http://www.itl.nist.gov/div898/handbook/, August 4.

8. Air Tox Environmental Company, Inc. Test Report Boiler MACT Demonstration Test Program For Cytec

Industries. October 2009.
Appendix A-1a: Mercury Fuel Analysis Variability Factor Outlier Analysis

Column B C D E F G H I J

FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Parameter_N

ame

Hg Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max Hg 

Fuel-Based 

Emissions with 

Control Efficiency

(lbpermmBtu)

Fuel

Variability 

Factor

(H/G) Outlier?

LABoiseNewsprintDeRidder 69-03 Biomass

Stoker/SlopedGrate/Other Wood: Bark Mercury (Hg) 5.38E-08 5.67E-08 1.05 no Fuel Category 1st Q 3rd Q IQR 1.5IQR

Test for low 

outliers

Test for 

high 

outliers

Count of Units in Variability Analysis

ORFlakeboardEugene Boiler-2 Biomass

Dutch Oven/Susp. Burner

Natural gas/Wood: Sanderdust Mercury (Hg) 9.00E-08 1.18E-07 1.31 no Biomass 1.12 1.24 0.13 0.19 0.90 1.48 8

MESDWarrenSomerset

No2 Power Boiler Biomass

Stoker/SlopedGrate/Other Biomass Mercury (Hg) 1.21E-07 1.47E-07 1.22 no Coal 1.29 2.80 1.52 2.28 (1.64) 9.19 24

KYNewPageWickliffe B09 Biomass Stoker/Slope dGrate/Other Wood: Bark Mercury (Hg) 2.17E-07 1.08E-05 49.82 yes Liquid 2.12 3.51 1.39 2.08 (2.29) 10.81 2GATempleInlandRome WF Biomass FB Wood: Bark Mercury (Hg) 3.30E-07 4.48E-07 1.36 no

TNBowaterNewsprint

Bubbling Fluidized Bed Boiler Biomass FB

Industrial Sludge/Tire Derived Fuel (TDF)/Wood: Bark Mercury (Hg) 3.33E-07 1.54E-06 4.64 yes

MEBoralexStratton Boiler #1 Biomass

Stoker/SlopedGrate/Other

Wood: Unadulterated Lumber Mercury (Hg) 3.42E-07 3.50E-07 1.02 no

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Biomass FB Biomass Mercury (Hg) 4.47E-07 4.56E-07 1.02 no

GAGPMadisonPly

800 Wood Waste Boiler Biomass

Stoker/SlopedGrate/Other Wood: Bark Mercury (Hg) 5.70E-07 8.85E-07 1.55 yes

ARAnthonyForestProducts SN-12 Biomass Fuel Cell

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber Mercury (Hg) 7.61E-07 1.36E-06 1.79 yes

ARGBPMorrilton SN-04 Biomass

Stoker/SlopedGrate/Other Wood: Bark Mercury (Hg) 1.01E-06 1.43E-06 1.41 no

ORRosboroSpringfield DV 01.1 Biomass

Dutch Oven/Susp. Burner

Hog Fuel/Natural gas Mercury (Hg) 1.53E-06 2.22E-06 1.45 no

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Coal FB

Coal: Subbituminous Mercury (Hg) 2.80E-08 4.21E-08 1.50 no

IAUofIowa EP7 Boiler 11 Coal FB

Coal: Bituminous Mercury (Hg) 5.99E-08 1.62E-07 2.70 no

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Coal FB

Coal: Bituminous Mercury (Hg) 6.34E-08 8.13E-07 12.83 yes

IAADMCornProcessingCR EU-501B Coal FB

Coal: Subbituminous Mercury (Hg) 8.18E-08 1.21E-07 1.48 no

INPurdueUniverisity Boiler 5 Coal FB

Coal: Bituminous Mercury (Hg) 1.35E-07 3.54E-07 2.63 no

ILPolyOne B1 Coal FB

Coal: Bituminous Mercury (Hg) 1.62E-07 1.71E-07 1.06 no

NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 1.85E-07 2.00E-07 1.08 no

SCCogenSouth

B001 - Main Boiler Coal PC

Coal: Bituminous Mercury (Hg) 2.50E-07 3.62E-07 1.45 no

MITBSimonPowerPlant Unit 1 Coal PC

Coal: Bituminous Mercury (Hg) 2.70E-07 9.35E-07 3.46 no
Appendix A-1a: Mercury Fuel Analysis Variability Factor Outlier Analysis

Column B C D E F G H I J

FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Parameter_N

ame

Hg Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max Hg 

Fuel-Based 

Emissions with 

Control Efficiency

(lbpermmBtu)

Fuel

Variability 

Factor

(H/G) Outlier?

IAMonsantoMuscatine

Boiler #8 (EP195) Coal Stoker/Slope dGrate/Other Industrial Sludge Mercury (Hg) 3.29E-07 5.18E-07 1.57 no

VAUniversityofVirginia 7103-1-01R Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 3.67E-07 9.83E-07 2.68 no

TNCargillMemphis

Stoker Boiler 8001 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 4.10E-07 6.72E-07 1.64 no

GASPNewsprint PB2 Coal FB

Coal: Bituminous Mercury (Hg) 4.19E-07 4.19E-07 1.00 no

TNEastman_NO_CBIDATA Boiler 30 Coal PC

Coal: Bituminous Mercury (Hg) 5.49E-07 2.75E-06 5.02 no

PAPHGlatfelter PB5 Coal FB

Coal: Bituminous Mercury (Hg) 5.89E-07 7.22E-07 1.23 no

NCUNCCogen ES-001 Coal FB

Coal: Bituminous Mercury (Hg) 8.29E-07 1.13E-06 1.36 no

IAUofNorthernIowa Boiler #3 Coal PC

Coal: Bituminous Mercury (Hg) 9.09E-07 1.08E-06 1.19 no

MNVersoPaper EU006 B&W Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 9.53E-07 9.53E-07 1.00 no

WVPPGMartinsville R011-Boiler 3 Coal PC

Coal: Bituminous Mercury (Hg) 1.10E-06 5.15E-06 4.66 no

VASmurfitStoneWestpt PB08 Coal PC

Coal: Bituminous Mercury (Hg) 1.22E-06 1.15E-05 9.44 yes

NCBlueRidgePaper G11042 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 1.49E-06 4.34E-06 2.91 no

VAINVISTAWaynesboro

2-205 (B#2) Boiler #2 Coal PC

Coal: Bituminous Mercury (Hg) 2.74E-06 7.02E-06 2.56 no

WINewPageBiron B24 Coal

Stoker/SlopedGrate/Other

Coal: Subbituminous Mercury (Hg) 2.91E-06 3.83E-06 1.32 no

WVATKRocketCenter

NB2766 W17479-W (Boiler 17) Coal

Stoker/SlopedGrate/Other

Coal: Bituminous/Plant-based Agricultural Residue Mercury (Hg) 4.31E-06 6.10E-06 1.41 no

INNotreDame B-4 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 5.30E-06 5.99E-03 1,131.07 yes

NCMillerCoors

ES-2 Coal/No. 2 & 6 Fuel Oil Boiler Coal PC

Coal: Bituminous Mercury (Hg) 6.23E-06 7.82E-06 1.26 no

OHMortonSaltRittman

B002 - CoalFired Boiler #2 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Mercury (Hg) 1.35E-05 3.38E-05 2.50 no

MEFPLEnergyWyman Unit #5 Liquid N/A

No. 6 Residual oil Mercury (Hg) 1.05E-07 1.51E-07 1.43 no

WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10 Liquid N/A

Deinking residuals Mercury (Hg) 5.88E-06 2.47E-05 4.20 no
Appendix A-1b: Chlorine Fuel Analysis Variability Factor Outlier Analysis

Column B C D E F G H I J

FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Parameter_N

ame

HCl Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max HCl

Fuel-Based 

Emissions with

Control 

Efficiency 

(lbpermmBtu)

Fuel

Variability Outlier

LABoiseNewsprintDeRidder 69-03 Biomass

Stoker/SlopedGrate/Other Wood: Bark Chlorine (Cl) 1.40E-05 2.47E-05 2.80E+00 no

Fuel 

Category 1st Q 3rd Q IQR 1.5IQR

Test for low 

outliers

Test for high 

outliers

Count of Units in Variability Analysis

SCMarlboroPaper

Hogged Fuel Boiler Biomass

Stoker/SlopedGrate/Other

Wood: Plywood, Particleboard (containing glues or resins) Chlorine (Cl) 1.00E-04 1.00E-04 1.91E+00 no Biomass 1.13E+00 2.02E+00 8.93E-01 1.34E+00 -3.82E-01 4.72E+00 1.10E+01

GAGPMadisonPly

800 Wood Waste Boiler Biomass

Stoker/SlopedGrate/Other Wood: Bark Chlorine (Cl) 1.05E-04 1.32E-04 1.26E+00 no Coal 1.12E+00 2.07E+00 9.44E-01 1.42E+00 -4.67E-01 4.99E+00 1.50E+01

ARAnthonyForestProducts SN-12 Biomass Fuel Cell

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber Chlorine (Cl) 2.00E-04 1.09E-03 1.00E+00 no Liquid 1.17E+00 3.14E+00 1.97E+00 2.95E+00 -2.29E+00 1.24E+01 4.00E+00

ORFlakeboardEugene Boiler-2 Biomass

Dutch Oven/Susp. Burner

Natural gas/Wood: Sanderdust Chlorine (Cl) 2.62E-04 2.86E-04 1.77E+00 no

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Biomass Fuel Cell

Hog Fuel/Natural gas Chlorine (Cl) 2.67E-04 3.03E-04 1.43E+00 no

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Biomass FB Biomass Chlorine (Cl) 3.56E-04 8.33E-04 5.44E+00 yes

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Biomass Fuel Cell

Hog Fuel/Natural gas Chlorine (Cl) 5.07E-04 7.24E-04 1.09E+00 no

ARWeyerhaeuserDierksMillSN-45 Biomass Fuel Cell

Hog Fuel/Natural gas Chlorine (Cl) 1.00E-03 1.91E-03 1.20E+00 no

KYNewPageWickliffe B09 Biomass Stoker/Slope dGrate/Other Wood: Bark Chlorine (Cl) 2.10E-03 2.10E-03 1.14E+00 noSCBowaterCoatedPaper

Combination Boiler No. 2 Biomass

Stoker/SlopedGrate/Other Wood: Bark Chlorine (Cl) 5.27E-03 6.30E-03 2.34E+00 no

ORRosboroSpringfield DV 01.1 Biomass

Dutch Oven/Susp. Burner

Hog Fuel/Natural gas Chlorine (Cl) 5.60E-03 1.57E-02 1.00E+00 no

TNEastman_NO_CBIDATA Boiler 30 Coal PC

Coal: Bituminous Chlorine (Cl) 7.23E-05 7.71E-04 1.85E+00 no

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Coal FB

Coal: Bituminous Chlorine (Cl) 8.56E-05 1.77E-04 2.14E+00 no

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Coal FB

Coal: Subbituminous Chlorine (Cl) 3.88E-04 4.12E-04 1.00E+00 no
Appendix A-1b: Chlorine Fuel Analysis Variability Factor Outlier Analysis

Column B C D E F G H I J

FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Parameter_N

ame

HCl Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max HCl

Fuel-Based 

Emissions with

Control 

Efficiency 

(lbpermmBtu)

Fuel

Variability Outlier

VAUniversityofVirginia 7103-1-01R Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Chlorine (Cl) 5.69E-04 6.56E-04 1.06E+00 no

VASmurfitStoneWestpt PB08 Coal PC

Coal: Bituminous Chlorine (Cl) 6.69E-04 7.45E-04 2.10E+00 no

NCBlueRidgePaper G11042 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Chlorine (Cl) 9.57E-04 1.77E-03 2.07E+00 no

SCCogenSouth

B001 - Main Boiler Coal PC

Coal: Bituminous Chlorine (Cl) 1.58E-03 1.78E-03 6.25E+00 yes

WINewPageBiron B24 Coal

Stoker/SlopedGrate/Other

Coal: Subbituminous Chlorine (Cl) 2.00E-03 4.27E-03 1.15E+00 no

INPurdueUniverisity Boiler 5 Coal FB

Coal: Bituminous Chlorine (Cl) 4.33E-03 2.71E-02 1.11E+00 no

PAAppletonPapers #036 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Chlorine (Cl) 7.83E-03 7.83E-03 1.36E+00 no

PAPHGlatfelter PB5 Coal FB Wood: Bark Chlorine (Cl) 2.86E-02 3.37E-02 1.07E+01 yesNCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Chlorine (Cl) 3.09E-02 4.21E-02 1.59E+00 no

GASPNewsprint PB2 Coal FB

Industrial Sludge Chlorine (Cl) 3.74E-02 3.74E-02 1.00E+00 no

WVPPGMartinsville R011-Boiler 3 Coal PC

Coal: Bituminous Chlorine (Cl) 4.67E-02 7.44E-02 1.18E+00 no

MOMallinckrodt Boiler 6 Coal

Stoker/SlopedGrate/Other

Coal: Subbituminous Chlorine (Cl) 1.12E-01 1.26E-01 1.35E+00 no

IAMonsantoMuscatine

Boiler #8 (EP195) Coal Stoker/Slope dGrate/Other Coal: Bituminous Chlorine (Cl) 1.22E-01 2.57E-01 1.12E+00 no

TNCargillMemphis

Stoker Boiler 8001 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous Chlorine (Cl) 1.28E-01 1.73E-01 1.13E+00 no

TNInvistaChattanooga

EU003 - Vaporizer #2 Liquid N/A

No. 2 Distillate Chlorine (Cl) 6.24E-04 1.54E-03 1.02E+00 no

NCInvistaHwy421 B7600 Liquid N/A

No. 6 Residual oil Chlorine (Cl) 8.25E-04 8.41E-04 2.46E+00 no

SCGPChemRussellville FO Boiler Liquid N/A Diesel fuel Chlorine (Cl) 1.00E-03 5.17E-03 1.22E+00 noWIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10 Liquid N/A

Deinking residuals Chlorine (Cl) 1.76E-03 2.15E-03 5.17E+00 no
Appendix A-2a: Mercury Fuel Analysis Variability Factor for Existing Units

Column B C D E F G H I J

Unit in Top 

12 percent? FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Hg Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max Hg 

Fuel-Based 

Emissions with 

Control Efficiency 

(lbpermmBtu)

Fuel

Variability 

Factor

(H/G) Outlier?

YES

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Biomass FB Biomass 4.47E-07 4.56E-07 1.02 no

YES

MESDWarrenSomerset

No2 Power Boiler Biomass

Stoker/SlopedGrate/Other Biomass 1.21E-07 1.47E-07 1.22 no Biomass 

YES

ORFlakeboardEugene Boiler-2 Biomass

Dutch Oven/Susp. Burner

Natural gas/Wood: Sanderdust 9.00E-08 1.18E-07 1.31 no Coal 

YES

GASPNewsprint PB2 Coal FB

Coal: Bituminous 4.19E-07 4.19E-07 1.00 no Liquid 

YES

MNVersoPaper EU006 B&W Coal

Stoker/SlopedGrate/Other

Coal: Bituminous 9.53E-07 9.53E-07 1.00 no

YES ILPolyOne B1 Coal FB

Coal: Bituminous 1.62E-07 1.71E-07 1.06 no

YES NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Coal

Stoker/SlopedGrate/Other

Coal: Bituminous 1.85E-07 2.00E-07 1.08 no

YES

NCUNCCogen ES-001 Coal FB

Coal: Bituminous 8.29E-07 1.13E-06 1.36 no

YES

SCCogenSouth

B001 - Main Boiler Coal PC

Coal: Bituminous 2.50E-07 3.62E-07 1.45 no

YES

IAADMCornProcessingCR EU-501B Coal FB

Coal: Subbituminous 8.18E-08 1.21E-07 1.48 no

YES

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Coal FB

Coal: Subbituminous 2.80E-08 4.21E-08 1.50 no

YES

IAMonsantoMuscatine

Boiler #8 (EP195) Coal Stoker/Slope dGrate/Other Industrial Sludge 3.29E-07 5.18E-07 1.57 no
Appendix A-2a: Mercury Fuel Analysis Variability Factor for Existing Units

Column B C D E F G H I J

Unit in Top 

12 percent? FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Hg Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max Hg 

Fuel-Based 

Emissions with 

Control Efficiency 

(lbpermmBtu)

Fuel

Variability 

Factor

(H/G) Outlier?

YES

TNCargillMemphis

Stoker Boiler 8001 Coal

Stoker/SlopedGrate/Other

Coal: Bituminous 4.10E-07 6.72E-07 1.64 no

YES

INPurdueUniverisity Boiler 5 Coal FB

Coal: Bituminous 1.35E-07 3.54E-07 2.63 no

YES

VAUniversityofVirginia 7103-1-01R Coal

Stoker/SlopedGrate/Other

Coal: Bituminous 3.67E-07 9.83E-07 2.68 no

YES IAUofIowa

EP7 Boiler 11 Coal FB

Coal: Bituminous 5.99E-08 1.62E-07 2.70 no

YES

MITBSimonPowerPlant Unit 1 Coal PC

Coal: Bituminous 2.70E-07 9.35E-07 3.46 no

YES

MEFPLEnergyWyman Unit #5 Liquid N/A

No. 6 Residual oil 1.05E-07 1.51E-07 1.43 no
Appendix A-2b: Mercury Fuel Analysis Variability Factor for New Units

Column B C D E F G H I J

Unit is Top 

Performer? FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

Hg Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max Hg 

Fuel-Based 

Emissions 

with Control 

Efficiency 

(lbpermmBtu)

Fuel

Variability 

Factor

(H/G) Outlier?

YES IAUofIowa

EP7 Boiler 11 Coal FB

Coal: Bituminous 5.99E-08 1.62E-07 2.70 no

Average Fuel Variability Factor for top 12 %

BiomassCoalLiquid

N/AN/A

2.70
Column B C D E F G H I J

Unit is Top 

Performer? FacilityID

CombustorID

_common

Fuel 

Category for 

Unit

Combustor 

Design

Common 

Fuel

HCl Average 

Emission 

Stack Test 

Results 

(lb/mmBtu)

Max HCl

Fuel-Based 

Emissions 

with Control 

Efficiency 

(lbpermmBtu)

Fuel

Variability 

Factor

(H/G) Outlier?

YES

WINewPa

geBiron B24 Coal

Stoker/Slo

pedGrate/

Other

Coal: Subbituminou

s 2.00E-03 4.27E-03 2.14 no

Average Fuel Variability Factor for 

top 12 %

YES

IAArchers

DanielsMi

dlandDes

Moines

Asea 

Boiler #1 Coal FB

Coal: Subbituminou

s 3.88E-04 4.12E-04 1.06 no Biomass N/A

YES

IARoquett

eAmerica

Circulating 

Fluidized 

Bed Boiler 

(121) Coal FB

Coal: 

Bituminou

s 8.56E-05 1.77E-04 2.07 no Coal 1.51 

YES

VAUnivers

ityofVirgini

a

7103-1-

01R Coal

Stoker/Slo

pedGrate/

Other

Coal: 

Bituminou

s 5.69E-04 6.56E-04 1.15 no Liquid 2.46 

YES

VASmurfit

StoneWes

tpt PB08 Coal PC

Coal: 

Bituminou

s 6.69E-04 7.45E-04 1.11 no

YES

TNInvista

Chattanoo

ga

EU003 - 

Vaporizer 

#2 liquid N/A

No. 2 

Distillate 6.24E-04 1.54E-03 2.46 no

Appendix A-2c: Chlorine Fuel Analysis Variability Factor for Existing Units, 
Appendix B-1: CO Emissions as a Function of Boiler Load 

GASES

CATesoro - CO by Load

Refinery Gas

0

0.1

0.2

0.3

0.4

0.5

0.6

0.7

70 71 72 73 74 75 76 77 78 79 80 81

Heat Input (mmBtu/hr)

CO Concentration (ppm @ 3% O2)

5.3

5.4

5.5

5.6

5.7

5.8

5.9

6

6.1

O2 %

CO

O2

WABOEINGRENTON: CO by Load

Natural Gas

0

5

10

15

20

25

30

35

40

45

50

0 10 20 30 40

Heat Input (mmBtu/hr)

CO Concentration (ppm @ 3% O2)

0

1

2

3

4

5

6

O2 %

CO

O2
Appendix B-1: CO Emissions as a Function of Boiler Load 

BIOMASS

TXDiboll Temple-Inland: CO by Load

Biomass - Dutch Oven/Susp. Burner

0

2000

4000

6000

8000

10000

12000

0 5 10 15 20 25 30 35

Heat Input (mmBtu/hr)

CO Concentration (ppm @ 3% O2)

0

2

4

6

8

10

12

14

16

O2 %

CO

O2

ARDomtarIndustries - CO by Load

Natural gas/Tire Derived Fuel (TDF)/Wood: Bark

Biomass - Stoker/SlopedGrate/Other

0

500

1000

1500

2000

2500

3000

3500

4000

4500

5000

0 100 200 300 400 500

Heat Input (mmBtu/hr)

CO Concentration (ppm @ 3% O2)

0

5

10

15

20

25

O2 %

CO

O2
Appendix B-1: CO Emissions as a Function of Boiler Load 

COAL

WVDupontWashingtonWorks: CO by Load

Coal: Stoker/SlopedGrate/Other

0

20

40

60

80

100

120

100 110 120 130 140 150 160 170 180 190 200

Heat Input (mmBtu/hr)

CO Concentration (ppm @ 3% O2)

0

2

4

6

8

10

12

O2 %

CO

O2

VAPhilipMorrisPark500: CO by Load

Coal - PC

0

10

20

30

40

50

60

100 200 300 400 500 600 700

Heat Input (mmBtu/hr)

CO Concentration (ppm @ 3% O2)

0

5

10

15

20

25

O2 %

CO

O2
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 382.7 6.9 11.92 17.4%

TXDibollTemple-Inland PB-44 2,473.4 9.3 13.13 23.2% Day

Daily Average CO 

Emission 

Concentration 

(ppm @ 3% O2)

TXDibollTemple-Inland PB-44 533.0 14.1 13.35 35.4% 1 448 

TXDibollTemple-Inland PB-44 250.9 15.0 12.02 37.4% 2 269 

TXDibollTemple-Inland PB-44 1,334.9 15.6 12.79 39.1% 3 179 

TXDibollTemple-Inland PB-44 391.4 16.6 13.29 41.4% 4 938 

TXDibollTemple-Inland PB-44 610.0 17.5 12.96 43.7% 5 215 

TXDibollTemple-Inland PB-44 187.0 17.8 12.06 44.6% 6 9,844 

TXDibollTemple-Inland PB-44 8,800.6 18.9 14.13 47.2% 7 7,352 

TXDibollTemple-Inland PB-44 6,599.8 18.9 13.98 47.2% 8 601 

TXDibollTemple-Inland PB-44 2,346.5 18.9 13.82 47.3% 9 331 

TXDibollTemple-Inland PB-44 9,259.8 18.9 14.23 47.3% 10 305 

TXDibollTemple-Inland PB-44 1,455.6 18.9 13.66 47.4% 11 294 

TXDibollTemple-Inland PB-44 7,698.9 19.0 14.07 47.4% 12 1,290 

TXDibollTemple-Inland PB-44 1,781.8 19.0 13.5 47.4% 13 1,321 

TXDibollTemple-Inland PB-44 518.7 19.0 13.3 47.4% 14 538 

TXDibollTemple-Inland PB-44 3,785.0 19.0 13.96 47.4% 15 581 

TXDibollTemple-Inland PB-44 9,978.6 19.0 14.26 47.5% 16 1,301 

TXDibollTemple-Inland PB-44 10,522.4 19.0 14.27 47.5% 17 2,877 

TXDibollTemple-Inland PB-44 7,715.0 19.0 14.07 47.5% 18 1,038 

TXDibollTemple-Inland PB-44 7,899.0 19.0 14.14 47.5% 19 511 

TXDibollTemple-Inland PB-44 4,572.2 19.0 14.06 47.5% 20 415 

TXDibollTemple-Inland PB-44 6,837.5 19.0 14.01 47.5% 21 161 

TXDibollTemple-Inland PB-44 942.0 19.0 13.47 47.5% 22 275 

TXDibollTemple-Inland PB-44 9,766.8 19.0 14.21 47.5% 23 159 

TXDibollTemple-Inland PB-44 10,675.2 19.0 14.26 47.5% 24 543 

TXDibollTemple-Inland PB-44 7,365.5 19.0 14.05 47.6% 25 273 

TXDibollTemple-Inland PB-44 6,728.7 19.0 14.01 47.6% 26 458 

TXDibollTemple-Inland PB-44 371.9 19.0 12.94 47.6% 27 298 

TXDibollTemple-Inland PB-44 7,229.0 19.1 14.06 47.7% 28 180 

TXDibollTemple-Inland PB-44 893.2 19.1 13.4 47.7% 29 255 

TXDibollTemple-Inland PB-44 2,114.9 19.1 13.5 47.7% 30 151 

TXDibollTemple-Inland PB-44 828.2 19.1 13.44 47.7%

30-day Average

(ppm @ 3% O2) 1,113 

TXDibollTemple-Inland PB-44 9,877.3 19.1 14.18 47.7%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 1,881.4 19.1 13.48 47.8%

TXDibollTemple-Inland PB-44 308.8 19.2 13.03 47.9%

TXDibollTemple-Inland PB-44 2,512.8 19.2 13.64 48.0%

TXDibollTemple-Inland PB-44 831.2 19.2 13.34 48.0%

TXDibollTemple-Inland PB-44 1,651.3 19.2 13.49 48.1%

TXDibollTemple-Inland PB-44 1,030.9 19.3 13.17 48.1%

TXDibollTemple-Inland PB-44 2,931.7 19.3 13.54 48.2%

TXDibollTemple-Inland PB-44 1,386.7 19.3 13.42 48.2%

TXDibollTemple-Inland PB-44 1,542.8 19.3 13.66 48.3%

TXDibollTemple-Inland PB-44 567.5 19.3 13 48.4%

TXDibollTemple-Inland PB-44 402.5 19.4 12.89 48.4%

TXDibollTemple-Inland PB-44 2,201.4 19.4 13.52 48.5%

TXDibollTemple-Inland PB-44 1,099.3 19.4 13.29 48.5%

TXDibollTemple-Inland PB-44 202.0 19.4 12.66 48.6%

TXDibollTemple-Inland PB-44 876.4 19.5 13.42 48.7%

TXDibollTemple-Inland PB-44 2,300.0 19.5 13.55 48.8%

TXDibollTemple-Inland PB-44 1,008.7 19.5 13.33 48.8%

TXDibollTemple-Inland PB-44 1,428.9 19.5 13.29 48.8%

TXDibollTemple-Inland PB-44 654.2 19.6 13.12 49.0%

TXDibollTemple-Inland PB-44 618.1 19.6 13.24 49.0%

TXDibollTemple-Inland PB-44 2,096.3 19.6 13.41 49.0%

TXDibollTemple-Inland PB-44 1,598.6 19.6 13.29 49.1%

TXDibollTemple-Inland PB-44 311.2 19.6 13.08 49.1%

TXDibollTemple-Inland PB-44 310.1 19.6 12.84 49.1%

TXDibollTemple-Inland PB-44 797.2 19.7 13.01 49.2%

TXDibollTemple-Inland PB-44 2,503.5 19.7 13.43 49.3%

TXDibollTemple-Inland PB-44 1,463.1 19.7 13.26 49.3%

TXDibollTemple-Inland PB-44 273.0 19.7 12.98 49.3%

TXDibollTemple-Inland PB-44 166.9 19.7 12.49 49.4%

TXDibollTemple-Inland PB-44 421.1 19.8 12.61 49.4%

TXDibollTemple-Inland PB-44 1,697.1 19.8 13.38 49.4%

TXDibollTemple-Inland PB-44 195.1 19.8 12.81 49.5%

TXDibollTemple-Inland PB-44 215.8 19.8 12.7 49.5%

TXDibollTemple-Inland PB-44 322.7 19.8 12.8 49.6%

TXDibollTemple-Inland PB-44 552.8 19.8 12.71 49.6%

TXDibollTemple-Inland PB-44 822.7 19.8 12.7 49.6%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 334.1 19.9 12.83 49.6%

TXDibollTemple-Inland PB-44 765.4 19.9 13.05 49.6%

TXDibollTemple-Inland PB-44 470.8 19.9 12.61 49.7%

TXDibollTemple-Inland PB-44 1,327.9 19.9 13.38 49.7%

TXDibollTemple-Inland PB-44 439.5 19.9 12.64 49.7%

TXDibollTemple-Inland PB-44 1,434.8 19.9 13.2 49.8%

TXDibollTemple-Inland PB-44 756.1 19.9 13.31 49.8%

TXDibollTemple-Inland PB-44 555.4 19.9 12.86 49.9%

TXDibollTemple-Inland PB-44 443.7 20.0 13.05 49.9%

TXDibollTemple-Inland PB-44 177.8 20.0 12.54 49.9%

TXDibollTemple-Inland PB-44 446.4 20.0 12.57 49.9%

TXDibollTemple-Inland PB-44 1,216.4 20.0 13.18 50.0%

TXDibollTemple-Inland PB-44 587.0 20.0 13.03 50.0%

TXDibollTemple-Inland PB-44 162.1 20.0 12.53 50.0%

TXDibollTemple-Inland PB-44 161.3 20.0 12.52 50.1%

TXDibollTemple-Inland PB-44 163.7 20.0 12.45 50.1%

TXDibollTemple-Inland PB-44 309.3 20.0 12.87 50.1%

TXDibollTemple-Inland PB-44 1,047.6 20.0 13.27 50.1%

TXDibollTemple-Inland PB-44 1,738.6 20.0 13.25 50.1%

TXDibollTemple-Inland PB-44 1,102.0 20.1 13.26 50.1%

TXDibollTemple-Inland PB-44 257.4 20.1 12.55 50.2%

TXDibollTemple-Inland PB-44 997.4 20.1 13.1 50.3%

TXDibollTemple-Inland PB-44 107.3 20.1 12.38 50.3%

TXDibollTemple-Inland PB-44 1,634.2 20.1 13.48 50.3%

TXDibollTemple-Inland PB-44 477.9 20.1 12.93 50.3%

TXDibollTemple-Inland PB-44 155.1 20.1 12.42 50.3%

TXDibollTemple-Inland PB-44 331.3 20.1 12.5 50.4%

TXDibollTemple-Inland PB-44 1,385.6 20.2 13.02 50.4%

TXDibollTemple-Inland PB-44 192.7 20.2 12.5 50.4%

TXDibollTemple-Inland PB-44 834.4 20.2 13.18 50.4%

TXDibollTemple-Inland PB-44 985.0 20.2 13.33 50.4%

TXDibollTemple-Inland PB-44 183.7 20.2 12.65 50.5%

TXDibollTemple-Inland PB-44 136.8 20.2 12.44 50.5%

TXDibollTemple-Inland PB-44 1,348.4 20.2 13.34 50.5%

TXDibollTemple-Inland PB-44 316.9 20.2 12.87 50.5%

TXDibollTemple-Inland PB-44 874.5 20.2 12.69 50.5%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 444.6 20.2 12.73 50.6%

TXDibollTemple-Inland PB-44 240.5 20.2 12.31 50.6%

TXDibollTemple-Inland PB-44 472.7 20.2 13.03 50.6%

TXDibollTemple-Inland PB-44 853.3 20.2 13.24 50.6%

TXDibollTemple-Inland PB-44 256.8 20.3 12.48 50.7%

TXDibollTemple-Inland PB-44 443.7 20.3 12.89 50.7%

TXDibollTemple-Inland PB-44 326.7 20.3 12.58 50.7%

TXDibollTemple-Inland PB-44 990.6 20.3 13.2 50.7%

TXDibollTemple-Inland PB-44 104.2 20.3 12.16 50.7%

TXDibollTemple-Inland PB-44 365.9 20.3 12.49 50.8%

TXDibollTemple-Inland PB-44 312.5 20.3 12.7 50.8%

TXDibollTemple-Inland PB-44 258.7 20.3 12.92 50.8%

TXDibollTemple-Inland PB-44 1,302.5 20.3 13.32 50.8%

TXDibollTemple-Inland PB-44 193.7 20.3 12.34 50.8%

TXDibollTemple-Inland PB-44 969.5 20.4 13.31 50.9%

TXDibollTemple-Inland PB-44 408.5 20.4 12.52 50.9%

TXDibollTemple-Inland PB-44 249.2 20.4 12.54 51.0%

TXDibollTemple-Inland PB-44 343.0 20.4 12.81 51.0%

TXDibollTemple-Inland PB-44 559.1 20.4 12.95 51.0%

TXDibollTemple-Inland PB-44 551.3 20.4 13.1 51.0%

TXDibollTemple-Inland PB-44 145.8 20.4 12.26 51.1%

TXDibollTemple-Inland PB-44 673.7 20.5 12.86 51.1%

TXDibollTemple-Inland PB-44 496.8 20.5 12.7 51.2%

TXDibollTemple-Inland PB-44 297.8 20.5 12.83 51.2%

TXDibollTemple-Inland PB-44 477.9 20.5 12.65 51.2%

TXDibollTemple-Inland PB-44 130.6 20.5 12.09 51.2%

TXDibollTemple-Inland PB-44 1,299.5 20.5 13.5 51.2%

TXDibollTemple-Inland PB-44 1,562.1 20.5 13.52 51.2%

TXDibollTemple-Inland PB-44 480.1 20.5 12.56 51.2%

TXDibollTemple-Inland PB-44 144.4 20.5 12.49 51.2%

TXDibollTemple-Inland PB-44 139.1 20.5 12.45 51.3%

TXDibollTemple-Inland PB-44 731.1 20.5 12.99 51.3%

TXDibollTemple-Inland PB-44 428.7 20.5 12.52 51.3%

TXDibollTemple-Inland PB-44 170.5 20.5 12.33 51.3%

TXDibollTemple-Inland PB-44 529.0 20.5 12.82 51.3%

TXDibollTemple-Inland PB-44 223.2 20.6 12.63 51.4%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 550.7 20.6 12.6322 51.4%

TXDibollTemple-Inland PB-44 184.1 20.6 12.36 51.4%

TXDibollTemple-Inland PB-44 247.5 20.6 12.29 51.4%

TXDibollTemple-Inland PB-44 354.8 20.6 12.86 51.4%

TXDibollTemple-Inland PB-44 530.2 20.6 13.08 51.4%

TXDibollTemple-Inland PB-44 149.0 20.6 12.13 51.5%

TXDibollTemple-Inland PB-44 773.6 20.6 13.1 51.5%

TXDibollTemple-Inland PB-44 182.1 20.6 12.4 51.5%

TXDibollTemple-Inland PB-44 375.5 20.6 12.84 51.6%

TXDibollTemple-Inland PB-44 150.0 20.7 12.37 51.6%

TXDibollTemple-Inland PB-44 629.9 20.7 13.06 51.6%

TXDibollTemple-Inland PB-44 418.4 20.7 12.55 51.7%

TXDibollTemple-Inland PB-44 131.5 20.7 12.44 51.7%

TXDibollTemple-Inland PB-44 399.2 20.7 12.78 51.7%

TXDibollTemple-Inland PB-44 495.2 20.7 12.89 51.7%

TXDibollTemple-Inland PB-44 197.9 20.7 12.22 51.7%

TXDibollTemple-Inland PB-44 382.6 20.7 12.76 51.8%

TXDibollTemple-Inland PB-44 1,246.6 20.7 13.18 51.8%

TXDibollTemple-Inland PB-44 510.7 20.7 12.98 51.8%

TXDibollTemple-Inland PB-44 157.4 20.7 12.72 51.8%

TXDibollTemple-Inland PB-44 301.8 20.7 12.95 51.8%

TXDibollTemple-Inland PB-44 633.6 20.7 12.86 51.8%

TXDibollTemple-Inland PB-44 297.9 20.7 12.62 51.8%

TXDibollTemple-Inland PB-44 359.8 20.7 12.45 51.8%

TXDibollTemple-Inland PB-44 478.9 20.7 13.01 51.8%

TXDibollTemple-Inland PB-44 661.4 20.7 12.96 51.9%

TXDibollTemple-Inland PB-44 1,698.4 20.7 13.53 51.9%

TXDibollTemple-Inland PB-44 688.6 20.8 13.16 51.9%

TXDibollTemple-Inland PB-44 161.6 20.8 12.49 51.9%

TXDibollTemple-Inland PB-44 262.2 20.8 12.87 52.0%

TXDibollTemple-Inland PB-44 260.8 20.8 12.5 52.0%

TXDibollTemple-Inland PB-44 335.7 20.8 12.92 52.0%

TXDibollTemple-Inland PB-44 405.6 20.8 12.9 52.0%

TXDibollTemple-Inland PB-44 460.2 20.8 12.91 52.0%

TXDibollTemple-Inland PB-44 764.2 20.8 13 52.0%

TXDibollTemple-Inland PB-44 283.6 20.8 12.67 52.1%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 226.4 20.8 12.83 52.1%

TXDibollTemple-Inland PB-44 488.9 20.8 12.98 52.1%

TXDibollTemple-Inland PB-44 218.0 20.8 12.92 52.1%

TXDibollTemple-Inland PB-44 1,440.6 20.8 13.46 52.1%

TXDibollTemple-Inland PB-44 273.4 20.8 12.64 52.1%

TXDibollTemple-Inland PB-44 223.4 20.9 12.55 52.1%

TXDibollTemple-Inland PB-44 140.8 20.9 12.34 52.1%

TXDibollTemple-Inland PB-44 275.9 20.9 12.93 52.2%

TXDibollTemple-Inland PB-44 712.7 20.9 13.07 52.2%

TXDibollTemple-Inland PB-44 232.2 20.9 12.45 52.2%

TXDibollTemple-Inland PB-44 206.1 20.9 12.57 52.2%

TXDibollTemple-Inland PB-44 954.1 20.9 13.24 52.3%

TXDibollTemple-Inland PB-44 655.5 20.9 13.05 52.3%

TXDibollTemple-Inland PB-44 841.1 20.9 12.95 52.3%

TXDibollTemple-Inland PB-44 564.5 20.9 12.91 52.3%

TXDibollTemple-Inland PB-44 1,495.6 20.9 13.36 52.3%

TXDibollTemple-Inland PB-44 466.9 20.9 12.78 52.3%

TXDibollTemple-Inland PB-44 324.5 20.9 12.6 52.3%

TXDibollTemple-Inland PB-44 280.8 20.9 12.58 52.4%

TXDibollTemple-Inland PB-44 721.2 20.9 13.06 52.4%

TXDibollTemple-Inland PB-44 82.8 21.0 11.98 52.4%

TXDibollTemple-Inland PB-44 205.9 21.0 12.17 52.4%

TXDibollTemple-Inland PB-44 179.2 21.0 12.65 52.4%

TXDibollTemple-Inland PB-44 235.0 21.0 12.42 52.4%

TXDibollTemple-Inland PB-44 232.0 21.0 12.2 52.5%

TXDibollTemple-Inland PB-44 160.2 21.0 12.45 52.5%

TXDibollTemple-Inland PB-44 729.0 21.0 12.89 52.5%

TXDibollTemple-Inland PB-44 1,248.3 21.0 13.44 52.5%

TXDibollTemple-Inland PB-44 335.4 21.0 12.98 52.5%

TXDibollTemple-Inland PB-44 1,133.2 21.0 12.97 52.5%

TXDibollTemple-Inland PB-44 300.8 21.0 12.64 52.5%

TXDibollTemple-Inland PB-44 243.5 21.0 12.78 52.6%

TXDibollTemple-Inland PB-44 328.8 21.0 12.84 52.6%

TXDibollTemple-Inland PB-44 310.7 21.0 12.48 52.6%

TXDibollTemple-Inland PB-44 348.0 21.1 12.3 52.6%

TXDibollTemple-Inland PB-44 275.3 21.1 12.29 52.6%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 108.5 21.1 12.42 52.7%

TXDibollTemple-Inland PB-44 241.3 21.1 12.21 52.7%

TXDibollTemple-Inland PB-44 401.2 21.1 12.75 52.7%

TXDibollTemple-Inland PB-44 187.9 21.1 12.1 52.7%

TXDibollTemple-Inland PB-44 461.7 21.1 12.82 52.8%

TXDibollTemple-Inland PB-44 696.6 21.1 12.95 52.8%

TXDibollTemple-Inland PB-44 322.6 21.1 12.29 52.8%

TXDibollTemple-Inland PB-44 1,754.3 21.1 13.28 52.8%

TXDibollTemple-Inland PB-44 243.8 21.1 12.85 52.9%

TXDibollTemple-Inland PB-44 190.2 21.1 12.64 52.9%

TXDibollTemple-Inland PB-44 611.4 21.2 13 52.9%

TXDibollTemple-Inland PB-44 431.0 21.2 12.85 53.0%

TXDibollTemple-Inland PB-44 203.4 21.2 12.62 53.0%

TXDibollTemple-Inland PB-44 268.8 21.2 12.15 53.0%

TXDibollTemple-Inland PB-44 768.9 21.2 12.97 53.0%

TXDibollTemple-Inland PB-44 680.4 21.2 12.99 53.0%

TXDibollTemple-Inland PB-44 289.0 21.2 12.2 53.1%

TXDibollTemple-Inland PB-44 127.6 21.2 12.26 53.1%

TXDibollTemple-Inland PB-44 215.2 21.3 12.25 53.1%

TXDibollTemple-Inland PB-44 412.2 21.3 12.6 53.2%

TXDibollTemple-Inland PB-44 307.7 21.3 12.18 53.2%

TXDibollTemple-Inland PB-44 188.8 21.3 12.06 53.2%

TXDibollTemple-Inland PB-44 841.9 21.3 13.07 53.2%

TXDibollTemple-Inland PB-44 258.4 21.3 12.57 53.2%

TXDibollTemple-Inland PB-44 589.1 21.3 12.81 53.3%

TXDibollTemple-Inland PB-44 198.2 21.3 12.11 53.3%

TXDibollTemple-Inland PB-44 437.6 21.3 12.78 53.3%

TXDibollTemple-Inland PB-44 264.0 21.3 12.53 53.3%

TXDibollTemple-Inland PB-44 368.8 21.3 12.83 53.3%

TXDibollTemple-Inland PB-44 370.8 21.3 12.82 53.3%

TXDibollTemple-Inland PB-44 342.0 21.3 12.87 53.3%

TXDibollTemple-Inland PB-44 422.1 21.4 12.31 53.4%

TXDibollTemple-Inland PB-44 366.0 21.4 12.25 53.4%

TXDibollTemple-Inland PB-44 263.9 21.4 12.57 53.4%

TXDibollTemple-Inland PB-44 57.0 21.4 12.88 53.4%

TXDibollTemple-Inland PB-44 359.3 21.4 12.89 53.5%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 383.9 21.4 12.41 53.5%

TXDibollTemple-Inland PB-44 73.0 21.4 12.16 53.5%

TXDibollTemple-Inland PB-44 667.0 21.4 13.03 53.5%

TXDibollTemple-Inland PB-44 209.5 21.4 12.61 53.5%

TXDibollTemple-Inland PB-44 60.9 21.4 12.67 53.5%

TXDibollTemple-Inland PB-44 341.5 21.4 12.83 53.6%

TXDibollTemple-Inland PB-44 238.0 21.4 12.19 53.6%

TXDibollTemple-Inland PB-44 568.3 21.4 12.54 53.6%

TXDibollTemple-Inland PB-44 359.1 21.4 12.46 53.6%

TXDibollTemple-Inland PB-44 392.6 21.5 12.82 53.6%

TXDibollTemple-Inland PB-44 207.5 21.5 12.32 53.7%

TXDibollTemple-Inland PB-44 158.3 21.5 12.22 53.7%

TXDibollTemple-Inland PB-44 306.7 21.5 12.72 53.7%

TXDibollTemple-Inland PB-44 989.0 21.5 13.01 53.7%

TXDibollTemple-Inland PB-44 273.6 21.5 12.54 53.7%

TXDibollTemple-Inland PB-44 353.8 21.5 12.72 53.7%

TXDibollTemple-Inland PB-44 243.6 21.5 11.96 53.7%

TXDibollTemple-Inland PB-44 224.4 21.5 12.34 53.7%

TXDibollTemple-Inland PB-44 197.0 21.5 12.29 53.7%

TXDibollTemple-Inland PB-44 135.9 21.5 12.18 53.7%

TXDibollTemple-Inland PB-44 883.5 21.5 13.06 53.8%

TXDibollTemple-Inland PB-44 476.7 21.5 12.77 53.8%

TXDibollTemple-Inland PB-44 267.1 21.5 12.69 53.9%

TXDibollTemple-Inland PB-44 282.4 21.6 12.87 53.9%

TXDibollTemple-Inland PB-44 237.5 21.6 12.51 53.9%

TXDibollTemple-Inland PB-44 360.6 21.6 12.68 53.9%

TXDibollTemple-Inland PB-44 280.3 21.6 12.92 54.0%

TXDibollTemple-Inland PB-44 693.2 21.6 12.85 54.0%

TXDibollTemple-Inland PB-44 230.3 21.6 12.38 54.0%

TXDibollTemple-Inland PB-44 1,371.1 21.6 13.11 54.0%

TXDibollTemple-Inland PB-44 281.0 21.6 12.3 54.0%

TXDibollTemple-Inland PB-44 208.8 21.6 12.68 54.0%

TXDibollTemple-Inland PB-44 161.2 21.6 12.24 54.1%

TXDibollTemple-Inland PB-44 159.4 21.6 12.39 54.1%

TXDibollTemple-Inland PB-44 560.4 21.6 12.86 54.1%

TXDibollTemple-Inland PB-44 432.8 21.6 12.73 54.1%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 485.4 21.7 12.69 54.1%

TXDibollTemple-Inland PB-44 487.0 21.7 12.66 54.1%

TXDibollTemple-Inland PB-44 647.8 21.7 12.8 54.2%

TXDibollTemple-Inland PB-44 639.5 21.7 12.58 54.2%

TXDibollTemple-Inland PB-44 211.1 21.7 12.54 54.2%

TXDibollTemple-Inland PB-44 66.6 21.7 12.82 54.2%

TXDibollTemple-Inland PB-44 936.0 21.7 12.73 54.2%

TXDibollTemple-Inland PB-44 291.7 21.7 12.09 54.2%

TXDibollTemple-Inland PB-44 352.3 21.7 12.5 54.2%

TXDibollTemple-Inland PB-44 232.6 21.7 12.15 54.2%

TXDibollTemple-Inland PB-44 365.9 21.7 12.68 54.3%

TXDibollTemple-Inland PB-44 307.1 21.7 12.83 54.3%

TXDibollTemple-Inland PB-44 236.1 21.7 12.58 54.3%

TXDibollTemple-Inland PB-44 348.0 21.7 12.7 54.3%

TXDibollTemple-Inland PB-44 300.3 21.7 12.53 54.3%

TXDibollTemple-Inland PB-44 130.7 21.7 12.51 54.4%

TXDibollTemple-Inland PB-44 250.9 21.7 12.27 54.4%

TXDibollTemple-Inland PB-44 484.2 21.7 12.82 54.4%

TXDibollTemple-Inland PB-44 152.0 21.8 12.32 54.4%

TXDibollTemple-Inland PB-44 980.8 21.8 13.29 54.4%

TXDibollTemple-Inland PB-44 619.0 21.8 13.09 54.5%

TXDibollTemple-Inland PB-44 235.5 21.8 12.9 54.5%

TXDibollTemple-Inland PB-44 374.1 21.8 12.16 54.5%

TXDibollTemple-Inland PB-44 215.3 21.8 12.26 54.6%

TXDibollTemple-Inland PB-44 441.1 21.9 12.97 54.7%

TXDibollTemple-Inland PB-44 133.6 21.9 12.21 54.8%

TXDibollTemple-Inland PB-44 163.7 21.9 12.58 54.8%

TXDibollTemple-Inland PB-44 283.8 21.9 12.87 54.8%

TXDibollTemple-Inland PB-44 398.1 22.0 12.56 54.9%

TXDibollTemple-Inland PB-44 258.9 22.0 12.78 54.9%

TXDibollTemple-Inland PB-44 257.2 22.0 12.08 55.0%

TXDibollTemple-Inland PB-44 600.9 22.0 12.63 55.0%

TXDibollTemple-Inland PB-44 273.5 22.0 12.72 55.0%

TXDibollTemple-Inland PB-44 382.0 22.0 12.67 55.0%

TXDibollTemple-Inland PB-44 139.3 22.0 12.41 55.0%

TXDibollTemple-Inland PB-44 245.4 22.0 12.5 55.0%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 222.2 22.0 12.87 55.1%

TXDibollTemple-Inland PB-44 133.4 22.0 12.4 55.1%

TXDibollTemple-Inland PB-44 346.6 22.0 12.68 55.1%

TXDibollTemple-Inland PB-44 5,002.2 22.0 13.6 55.1%

TXDibollTemple-Inland PB-44 102.0 22.0 11.88 55.1%

TXDibollTemple-Inland PB-44 121.1 22.1 12.25 55.1%

TXDibollTemple-Inland PB-44 348.8 22.1 12.68 55.2%

TXDibollTemple-Inland PB-44 185.4 22.1 12.5 55.2%

TXDibollTemple-Inland PB-44 118.7 22.1 12.42 55.2%

TXDibollTemple-Inland PB-44 226.9 22.1 11.93 55.3%

TXDibollTemple-Inland PB-44 127.0 22.1 12.45 55.3%

TXDibollTemple-Inland PB-44 184.0 22.1 12.43 55.3%

TXDibollTemple-Inland PB-44 500.6 22.1 12.81 55.3%

TXDibollTemple-Inland PB-44 192.9 22.1 12.8 55.4%

TXDibollTemple-Inland PB-44 140.2 22.1 12.45 55.4%

TXDibollTemple-Inland PB-44 98.2 22.2 12.16 55.5%

TXDibollTemple-Inland PB-44 1,057.5 22.2 12.95 55.5%

TXDibollTemple-Inland PB-44 126.5 22.2 12.18 55.6%

TXDibollTemple-Inland PB-44 626.0 22.2 12.64 55.6%

TXDibollTemple-Inland PB-44 162.4 22.2 12.39 55.6%

TXDibollTemple-Inland PB-44 248.6 22.3 12.51 55.7%

TXDibollTemple-Inland PB-44 306.4 22.3 12 55.7%

TXDibollTemple-Inland PB-44 365.7 22.3 12.49 55.7%

TXDibollTemple-Inland PB-44 355.9 22.3 12.73 55.7%

TXDibollTemple-Inland PB-44 309.2 22.3 12.87 55.8%

TXDibollTemple-Inland PB-44 289.5 22.3 12.12 55.8%

TXDibollTemple-Inland PB-44 221.9 22.3 12.5 55.8%

TXDibollTemple-Inland PB-44 187.3 22.3 12.53 55.8%

TXDibollTemple-Inland PB-44 1,169.1 22.3 13.14 55.8%

TXDibollTemple-Inland PB-44 207.0 22.4 12.61 55.9%

TXDibollTemple-Inland PB-44 136.4 22.4 12.32 55.9%

TXDibollTemple-Inland PB-44 267.4 22.4 12.69 55.9%

TXDibollTemple-Inland PB-44 173.0 22.4 12.43 56.0%

TXDibollTemple-Inland PB-44 257.0 22.4 12.35 56.1%

TXDibollTemple-Inland PB-44 193.7 22.4 12.53 56.1%

TXDibollTemple-Inland PB-44 119.0 22.4 12.02 56.1%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 573.2 22.5 12.88 56.1%

TXDibollTemple-Inland PB-44 133.3 22.5 12.66 56.2%

TXDibollTemple-Inland PB-44 216.6 22.5 12.61 56.2%

TXDibollTemple-Inland PB-44 123.5 22.5 12.41 56.2%

TXDibollTemple-Inland PB-44 587.8 22.5 12.81 56.2%

TXDibollTemple-Inland PB-44 555.5 22.5 12.82 56.2%

TXDibollTemple-Inland PB-44 1,184.8 22.5 13.12 56.3%

TXDibollTemple-Inland PB-44 257.0 22.5 12.66 56.3%

TXDibollTemple-Inland PB-44 186.8 22.5 12.06 56.3%

TXDibollTemple-Inland PB-44 61.4 22.5 12.18 56.3%

TXDibollTemple-Inland PB-44 154.6 22.5 12.48 56.4%

TXDibollTemple-Inland PB-44 777.4 22.6 12.68 56.4%

TXDibollTemple-Inland PB-44 459.8 22.6 12.6 56.4%

TXDibollTemple-Inland PB-44 153.6 22.6 12.31 56.5%

TXDibollTemple-Inland PB-44 3,153.0 22.6 13.38 56.5%

TXDibollTemple-Inland PB-44 278.6 22.6 12.54 56.5%

TXDibollTemple-Inland PB-44 154.6 22.6 12.25 56.5%

TXDibollTemple-Inland PB-44 707.3 22.6 12.79 56.5%

TXDibollTemple-Inland PB-44 3,636.3 22.6 13.45 56.5%

TXDibollTemple-Inland PB-44 281.1 22.6 12.61 56.6%

TXDibollTemple-Inland PB-44 148.1 22.6 12.25 56.6%

TXDibollTemple-Inland PB-44 113.6 22.7 12.26 56.7%

TXDibollTemple-Inland PB-44 322.2 22.7 12.45 56.7%

TXDibollTemple-Inland PB-44 56.5 22.7 11.96 56.7%

TXDibollTemple-Inland PB-44 99.3 22.7 12.17 56.7%

TXDibollTemple-Inland PB-44 410.6 22.7 12.98 56.8%

TXDibollTemple-Inland PB-44 218.3 22.7 12.08 56.8%

TXDibollTemple-Inland PB-44 381.1 22.7 12.78 56.8%

TXDibollTemple-Inland PB-44 361.6 22.7 12.64 56.8%

TXDibollTemple-Inland PB-44 177.7 22.7 11.96 56.8%

TXDibollTemple-Inland PB-44 177.4 22.7 12.28 56.8%

TXDibollTemple-Inland PB-44 399.6 22.7 12.91 56.9%

TXDibollTemple-Inland PB-44 128.4 22.7 12.12 56.9%

TXDibollTemple-Inland PB-44 73.2 22.8 12.19 56.9%

TXDibollTemple-Inland PB-44 129.0 22.8 12.29 57.0%

TXDibollTemple-Inland PB-44 397.3 22.8 12.86 57.0%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 403.2 22.8 12.89 57.0%

TXDibollTemple-Inland PB-44 185.9 22.8 12.56 57.1%

TXDibollTemple-Inland PB-44 301.4 22.8 12.78 57.1%

TXDibollTemple-Inland PB-44 163.8 22.9 11.75 57.2%

TXDibollTemple-Inland PB-44 151.5 22.9 12.11 57.2%

TXDibollTemple-Inland PB-44 2,257.3 22.9 13.26 57.2%

TXDibollTemple-Inland PB-44 115.9 22.9 12.35 57.2%

TXDibollTemple-Inland PB-44 189.1 22.9 12.53 57.3%

TXDibollTemple-Inland PB-44 188.5 22.9 12.36 57.3%

TXDibollTemple-Inland PB-44 126.8 22.9 12.05 57.4%

TXDibollTemple-Inland PB-44 510.6 23.0 12.5 57.4%

TXDibollTemple-Inland PB-44 152.4 23.0 12.54 57.4%

TXDibollTemple-Inland PB-44 158.7 23.0 12.25 57.4%

TXDibollTemple-Inland PB-44 241.3 23.0 12.25 57.5%

TXDibollTemple-Inland PB-44 275.6 23.0 11.99 57.5%

TXDibollTemple-Inland PB-44 244.7 23.0 12.16 57.5%

TXDibollTemple-Inland PB-44 254.0 23.0 12.41 57.5%

TXDibollTemple-Inland PB-44 388.2 23.0 11.99 57.6%

TXDibollTemple-Inland PB-44 128.6 23.0 12.48 57.6%

TXDibollTemple-Inland PB-44 155.2 23.0 12.27 57.6%

TXDibollTemple-Inland PB-44 310.4 23.1 12.62 57.6%

TXDibollTemple-Inland PB-44 632.3 23.1 12.93 57.7%

TXDibollTemple-Inland PB-44 206.1 23.1 12.01 57.7%

TXDibollTemple-Inland PB-44 378.8 23.1 12.67 57.7%

TXDibollTemple-Inland PB-44 86.4 23.1 12.05 57.8%

TXDibollTemple-Inland PB-44 208.5 23.1 12.6 57.8%

TXDibollTemple-Inland PB-44 455.3 23.1 12.85 57.8%

TXDibollTemple-Inland PB-44 930.2 23.1 12.83 57.8%

TXDibollTemple-Inland PB-44 120.0 23.2 12.13 57.9%

TXDibollTemple-Inland PB-44 217.9 23.2 12.69 58.0%

TXDibollTemple-Inland PB-44 330.9 23.2 12.13 58.0%

TXDibollTemple-Inland PB-44 102.1 23.2 11.99 58.0%

TXDibollTemple-Inland PB-44 409.1 23.2 12.35 58.0%

TXDibollTemple-Inland PB-44 192.8 23.2 12.43 58.0%

TXDibollTemple-Inland PB-44 199.7 23.2 12.51 58.0%

TXDibollTemple-Inland PB-44 255.5 23.2 12.41 58.1%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 188.4 23.3 12.32 58.1%

TXDibollTemple-Inland PB-44 599.5 23.3 12.49 58.1%

TXDibollTemple-Inland PB-44 178.6 23.3 12.26 58.2%

TXDibollTemple-Inland PB-44 68.7 23.3 12.16 58.2%

TXDibollTemple-Inland PB-44 127.2 23.3 12.16 58.2%

TXDibollTemple-Inland PB-44 723.2 23.3 12.8 58.2%

TXDibollTemple-Inland PB-44 237.7 23.3 12.32 58.2%

TXDibollTemple-Inland PB-44 80.5 23.3 11.97 58.2%

TXDibollTemple-Inland PB-44 201.4 23.3 12.51 58.2%

TXDibollTemple-Inland PB-44 480.2 23.3 12.89 58.2%

TXDibollTemple-Inland PB-44 610.1 23.3 12.49 58.2%

TXDibollTemple-Inland PB-44 386.7 23.3 12.29 58.4%

TXDibollTemple-Inland PB-44 341.8 23.4 12.25 58.4%

TXDibollTemple-Inland PB-44 177.5 23.4 12.03 58.4%

TXDibollTemple-Inland PB-44 463.8 23.4 12.71 58.5%

TXDibollTemple-Inland PB-44 169.9 23.4 11.78 58.5%

TXDibollTemple-Inland PB-44 188.1 23.5 12.27 58.7%

TXDibollTemple-Inland PB-44 232.2 23.5 12.44 58.7%

TXDibollTemple-Inland PB-44 153.5 23.5 12.1 58.7%

TXDibollTemple-Inland PB-44 173.9 23.5 12.19 58.7%

TXDibollTemple-Inland PB-44 158.7 23.5 12.22 58.8%

TXDibollTemple-Inland PB-44 296.4 23.5 12.71 58.8%

TXDibollTemple-Inland PB-44 142.7 23.5 11.83 58.9%

TXDibollTemple-Inland PB-44 180.7 23.6 12.58 58.9%

TXDibollTemple-Inland PB-44 164.4 23.6 12.28 58.9%

TXDibollTemple-Inland PB-44 107.2 23.6 11.73 58.9%

TXDibollTemple-Inland PB-44 145.2 23.6 12.35 58.9%

TXDibollTemple-Inland PB-44 126.4 23.6 12.49 59.0%

TXDibollTemple-Inland PB-44 35.2 23.6 11.32 59.0%

TXDibollTemple-Inland PB-44 373.5 23.6 12.62 59.0%

TXDibollTemple-Inland PB-44 212.3 23.6 12.48 59.0%

TXDibollTemple-Inland PB-44 178.2 23.6 12.28 59.1%

TXDibollTemple-Inland PB-44 717.3 23.6 12.74 59.1%

TXDibollTemple-Inland PB-44 116.2 23.6 11.99 59.1%

TXDibollTemple-Inland PB-44 195.7 23.7 11.96 59.2%

TXDibollTemple-Inland PB-44 133.9 23.7 11.83 59.2%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 121.1 23.7 11.93 59.2%

TXDibollTemple-Inland PB-44 110.9 23.7 12.05 59.3%

TXDibollTemple-Inland PB-44 120.6 23.7 12.04 59.3%

TXDibollTemple-Inland PB-44 390.2 23.7 12.35 59.3%

TXDibollTemple-Inland PB-44 209.0 23.7 12.41 59.4%

TXDibollTemple-Inland PB-44 2,197.6 23.8 13.29 59.4%

TXDibollTemple-Inland PB-44 182.2 23.8 12.25 59.5%

TXDibollTemple-Inland PB-44 97.8 23.8 12.04 59.5%

TXDibollTemple-Inland PB-44 468.0 23.8 12.34 59.5%

TXDibollTemple-Inland PB-44 126.1 24.0 12.01 59.9%

TXDibollTemple-Inland PB-44 483.0 24.0 12.35 60.0%

TXDibollTemple-Inland PB-44 117.5 24.0 11.9 60.0%

TXDibollTemple-Inland PB-44 156.1 24.0 12.19 60.1%

TXDibollTemple-Inland PB-44 315.8 24.0 12.53 60.1%

TXDibollTemple-Inland PB-44 2,588.8 24.0 13.31 60.1%

TXDibollTemple-Inland PB-44 2,727.8 24.0 13.35 60.1%

TXDibollTemple-Inland PB-44 119.0 24.1 11.95 60.2%

TXDibollTemple-Inland PB-44 482.6 24.1 12.37 60.3%

TXDibollTemple-Inland PB-44 192.5 24.1 12.1 60.4%

TXDibollTemple-Inland PB-44 1,929.0 24.2 13.11 60.4%

TXDibollTemple-Inland PB-44 3,059.8 24.2 13.4 60.5%

TXDibollTemple-Inland PB-44 94.1 24.2 11.92 60.5%

TXDibollTemple-Inland PB-44 456.3 24.3 12.42 60.7%

TXDibollTemple-Inland PB-44 198.7 24.3 12.46 60.7%

TXDibollTemple-Inland PB-44 133.3 24.3 11.93 60.7%

TXDibollTemple-Inland PB-44 27.1 24.3 10.6 60.7%

TXDibollTemple-Inland PB-44 2,254.0 24.5 13.31 61.2%

TXDibollTemple-Inland PB-44 780.5 24.5 12.71 61.2%

TXDibollTemple-Inland PB-44 454.9 24.5 12.38 61.2%

TXDibollTemple-Inland PB-44 103.7 24.6 12.02 61.6%

TXDibollTemple-Inland PB-44 3,531.1 24.7 13.43 61.6%

TXDibollTemple-Inland PB-44 113.1 24.7 11.91 61.8%

TXDibollTemple-Inland PB-44 129.7 24.7 11.86 61.9%

TXDibollTemple-Inland PB-44 292.0 24.8 12.01 61.9%

TXDibollTemple-Inland PB-44 406.3 24.8 12.35 61.9%

TXDibollTemple-Inland PB-44 111.4 24.9 12.04 62.2%
Appendix B-2: CO 30-Day Average for TXDibollTemple-Inland

FacilityID CombustorID

CO 

(ppm@3%O2) Heat_Input O2% % of Design Capacity

TXDibollTemple-Inland PB-44 1,566.1 24.9 13.04 62.2%

TXDibollTemple-Inland PB-44 104.7 24.9 11.9 62.3%

TXDibollTemple-Inland PB-44 2,843.8 25.0 13.34 62.4%

TXDibollTemple-Inland PB-44 118.6 25.0 11.57 62.5%

TXDibollTemple-Inland PB-44 169.3 25.0 12.09 62.5%

TXDibollTemple-Inland PB-44 125.6 25.0 11.96 62.6%

TXDibollTemple-Inland PB-44 102.6 25.1 11.95 62.8%

TXDibollTemple-Inland PB-44 1,481.7 25.2 13.08 62.9%

TXDibollTemple-Inland PB-44 132.4 25.3 11.42 63.3%

TXDibollTemple-Inland PB-44 101.5 25.4 11.6 63.6%

TXDibollTemple-Inland PB-44 1,499.4 25.4 12.95 63.6%

TXDibollTemple-Inland PB-44 112.3 25.5 11.66 63.7%

TXDibollTemple-Inland PB-44 95.9 25.7 11.67 64.1%

TXDibollTemple-Inland PB-44 147.0 25.7 11.53 64.2%

TXDibollTemple-Inland PB-44 72.2 25.9 11.7 64.8%

TXDibollTemple-Inland PB-44 64.5 26.0 11.67 64.9%

TXDibollTemple-Inland PB-44 39.3 26.3 11.34 65.7%

TXDibollTemple-Inland PB-44 9.9 27.1 10.6 67.7%

TXDibollTemple-Inland PB-44 5.6 29.1 9.75 72.7%

TXDibollTemple-Inland PB-44 6.8 29.5 9.81 73.7%

TXDibollTemple-Inland PB-44 18.2 29.8 9.24 74.6%

TXDibollTemple-Inland PB-44 25.3 30.0 9.81 74.9%

TXDibollTemple-Inland PB-44 11.0 30.9 9.89 77.3%

TXDibollTemple-Inland PB-44 11.0 31.0 9.32 77.6%

TXDibollTemple-Inland PB-44 16.9 31.0 9.03 77.6%
Appendix C-1: Summary of Number of Sources with Test Data and Top 12 Percent

MACT Floor by Fuel Type

Parameters

PM 

Filterable

(lb/mmBtu) Hg HCl CO

D/F 

total mass

D/F

TEQ

Total Count of 

Units in 

Subcategory

Biomass 420

No. of sources = 192 91 92

No. in MACT floor = 24 11 12 0

Coal 578

No. of sources = 366 285 318

No. in MACT floor = 44 35 39 0

Liquid 826

No. of sources = 91 177 190 116 17 17

No. in MACT floor = 11 22 23 14 3 3

Gas 1 - Excluding Metal Industry Furnaces 10783

No. of sources = 144 14 11 754 8 8

No. in MACT floor = 18 2 2 91 1 1

Gas 1 - Metal Industry Furnaces 749

No. of sources = 9 7 9 15 7 7

No. in MACT floor = 2 1 2 2 1 1

Gas 2 199

No. of sources = 13 8 8 75 5 5

No. in MACT floor = 2 1 1 9 1 1

Parameters

CO (ppm @ 

3% O2)

Dioxin/Fura

ns (Total 

Mass)

ppm@ 3% 

O2)

Dioxin/Fura

ns (TEQ)

ppm@ 3% 

O2)

Total Count of 

Units in 

Subcategory

Biomass - Dutch Oven 62

No. of sources = 17 3 3

No. in MACT floor = 3 1 1

Biomass - Fluidized Bed 12

No. of sources = 7 6 6

No. in MACT floor = 5 5 5

Biomass - Fuel Cell 26

No. of sources = 16 7 7

No. in MACT floor = 5 5 5

Biomass - Stoker 320

No. of sources = 119 16 16

No. in MACT floor = 15 2 2

Coal - FB 31

No. of sources = 17 12 12

No. in MACT floor = 3 2 2

Coal - PC 186

No. of sources = 41 10 10

No. in MACT floor = 5 2 2

Coal - Stoker 361

No. of sources = 61 14 14

No. in MACT floor = 8 2 2
APPENDIX C-2 

Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis 

According to Fuel Type 

(See file named “mjr-MACT Floor Appx C-2” for facility-specific cost estimates)
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

FLUSSugarC

orp Boiler No. 7 CO Biomass

Dutch 

Oven/Susp. 

Burner 1.87E+01 1 YES

TXDibollTem

ple-Inland PB-44 CO Biomass

Dutch 

Oven/Susp. 

Burner 6.93E+01 2 YES

WAGraysHar

borPaper

No. 6 Boiler 

(EU2) CO Biomass

Dutch 

Oven/Susp. 

Burner 2.56E+02 3 YES

FLSugarCan

eGrowersCo

op Boiler No. 8 CO Biomass

Dutch 

Oven/Susp. 

Burner 3.17E+02 4 NO

ORRosboroS

pringfield DV 01.1 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.10E+02 5 NO

ORFlakeboar

dEugene Boiler-2 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.48E+02 6 NO

FLUSSugarC

orp Boiler No. 8 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.51E+02 7 NO

OHSauderW

oodArchbold B009 CO Biomass

Dutch 

Oven/Susp. 

Burner 5.02E+02 8 NO

OHSauderW

oodArchbold B008 CO Biomass

Dutch 

Oven/Susp. 

Burner 5.42E+02 9 NO

MNNorbordM

innesota Konus No. 1 CO Biomass

Dutch 

Oven/Susp. 

Burner 9.60E+02 10 NO

MNNorbordM

innesota Konus No. 2 CO Biomass

Dutch 

Oven/Susp. 

Burner 9.60E+02 11 NO

FLUSSugarC

orp Boiler No. 4 CO Biomass

Dutch 

Oven/Susp. 

Burner 1.48E+03 12 NO

FLSugarCan

eGrowersCo

op Boiler No. 1 CO Biomass

Dutch 

Oven/Susp. 

Burner 2.35E+03 13 NO

FLOsceolaF

arms Boiler No. 3 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.26E+03 14 NO

FLUSSugarC

orp Boiler No. 1 CO Biomass

Dutch 

Oven/Susp. 

Burner 7.37E+03 15 NO

FLOsceolaF

arms Boiler No. 6 CO Biomass

Dutch 

Oven/Susp. 

Burner 7.50E+03 16 NO

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

FLUSSugarC

orp Boiler No. 2 CO Biomass

Dutch 

Oven/Susp. 

Burner 1.98E+04 17 NO

ORGeorgiaP

acificWauna

Mill

EU35 - 

Fluidized 

Bed Boiler CO Biomass FB 2.39E+01 1 YES

ALIPCourtlan

d

No. 3 

Combination 

Boier / 

11CU301 CO Biomass FB 3.98E+01 2 YES

TNDomtar23

84 HFB1-1 CO Biomass FB 8.17E+01 3 YES

GATempleInl

andRome WF CO Biomass FB 9.88E+01 4 YES

KYDomtarHa

wesville

Biofuel Boiler 

B-900 CO Biomass FB 1.12E+02 5 YES

TNBowaterN

ewsprint

Bubbling 

Fluidized 

Bed Boiler CO Biomass FB 1.15E+02 6 NO

NDCargillWe

stFargo

Foster 

Wheeler 

Boiler 

(EU43) CO Biomass FB 3.55E+03 7 NO

KYWeyerhae

userEKY MP 01-01 CO Biomass Fuel Cell 5.74E+01 1 YES

KYWeyerhae

userEKY MP 01-03 CO Biomass Fuel Cell 5.74E+01 2 YES

ARWeyerhae

userDierksMi

ll SN-45 CO Biomass Fuel Cell 6.21E+01 3 YES

WAWeyerha

euser_Raym

ond

Hog Fuel 

Boiler EU1 CO Biomass Fuel Cell 1.16E+02 4 YES

WVGPMtHo

peOSB

5600 - 

Wellons 

Energy 

System CO Biomass Fuel Cell 1.27E+02 5 YES

VAGeorgiaP

acificBrookn

ealGladys 5600 CO Biomass Fuel Cell 1.73E+02 6 NO

MSWeyerha

euserBruce

AA-002 No. 

2 Boiler CO Biomass Fuel Cell 1.87E+02 7 NO

IDPotlatch PB-1 CE CO Biomass Fuel Cell 2.72E+02 8 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

GAADMLoca

tion551 630- Wellons CO Biomass Fuel Cell 3.66E+02 9 NO

ORWeyerha

euserCoWarr

entonLumber

Mill 3-HFB CO Biomass Fuel Cell 4.55E+02 10 NO

ARAnthonyF

orestProduct

s SN-16 CO Biomass Fuel Cell 5.41E+02 11 NO

ARAnthonyF

orestProduct

s SN-12 CO Biomass Fuel Cell 6.54E+02 12 NO

MTPlumCree

k

Wellons 

Plywood CO Biomass Fuel Cell 1.19E+03 13 NO

TXNorbordT

exasNacogd

oches Konus No. 1 CO Biomass Fuel Cell 1.22E+03 14 NO

TXNorbordT

exasNacogd

oches Konus No. 2 CO Biomass Fuel Cell 1.22E+03 15 NO

NCUniboard

USA

Wellons 

Thermal Oil 

Heater CO Biomass Fuel Cell 1.58E+05 16 NO

GATempleInl

andThomson BW-B001 CO Biomass

Stoker/Slope

dGrate/Other 4.08E+00 1 YES

WVWeyerha

euserBuckha

nnon 001-01 CO Biomass

Stoker/Slope

dGrate/Other 2.28E+01 2 YES

WAKimberly

ClarkEverett

No. 14 

Cogeneration 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 3.39E+01 3 YES

IDChilcoLake

Sawmill HFB1 CO Biomass

Stoker/Slope

dGrate/Other 5.10E+01 4 YES

ARWestFras

erHuttig SN-24 CO Biomass

Stoker/Slope

dGrate/Other 6.48E+01 5 YES

MILPCSagol

a TOH-Wood CO Biomass

Stoker/Slope

dGrate/Other 6.80E+01 6 YES

INConsolidat

edGrainandB

arge P17B CO Biomass

Stoker/Slope

dGrate/Other 8.72E+01 7 YES

INConsolidat

edGrainandB

arge P17C CO Biomass

Stoker/Slope

dGrate/Other 8.72E+01 8 YES
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

MNAnderson

CorpBayport

Boiler 11 

EU620 CO Biomass

Stoker/Slope

dGrate/Other 9.25E+01 9 YES

MNAnderson

CorpBayport

Boiler 12 

EU621 CO Biomass

Stoker/Slope

dGrate/Other 9.96E+01 10 YES

MSGPNewA

ugusta

AA-015 

Power Boiler CO Biomass

Stoker/Slope

dGrate/Other 1.02E+02 11 YES

KYNewPageWickliffe B09 CO BiomassStoker/Slope

dGrate/Other 1.13E+02 12 YES

ALMeadwest

vacoCottonto

n46

No.3 Wood 

Residue 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 1.22E+02 13 YES

MSShuquala

kLumber

Boiler 4 (AA108) CO BiomassStoker/Slope

dGrate/Other 1.22E+02 14 YES

MSHoodBea

umont

AA-030 

(Wood-Fired 

Boiler) CO Biomass

Stoker/Slope

dGrate/Other 1.28E+02 15 YES

OHAkronThe

rmalEnergy

Unit #2 

(B004) CO Biomass

Stoker/Slope

dGrate/Other 1.29E+02 16 NO

GATempleInl

andRome PB4 CO Biomass

Stoker/Slope

dGrate/Other 1.30E+02 17 NO

MNWeyerha

euserIronton

EU 001 - 4 

Cell Furnace CO Biomass

Stoker/Slope

dGrate/Other 1.32E+02 18 NO

ORBlueHero

nPaper G Boiler CO Biomass

Stoker/Slope

dGrate/Other 1.47E+02 19 NO

MIWhitePine

Electric IBW Boiler CO Biomass

Stoker/Slope

dGrate/Other 1.49E+02 20 NO

PAProctorGa

mbleMehoop

anyPA

Boiler #3 

(033A) CO Biomass

Stoker/Slope

dGrate/Other 1.51E+02 21 NO

ALWestervel

t

Teaford - 

Unit 003 CO Biomass

Stoker/Slope

dGrate/Other 1.59E+02 22 NO

ALIPCourtlan

d

No. 1 

Combination 

Boiler / 

11CU101 CO Biomass

Stoker/Slope

dGrate/Other 1.60E+02 23 NO

IDRileyCreek

Lumber HFB1 CO Biomass

Stoker/Slope

dGrate/Other 1.61E+02 24 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

ORStimsonL

umberForest

Grove Boiler 1 CO Biomass

Stoker/Slope

dGrate/Other 1.64E+02 25 NO

ORStimsonL

umberForest

Grove Boiler 2 CO Biomass

Stoker/Slope

dGrate/Other 1.64E+02 26 NO

ORStimsonL

umberForest

Grove Boiler 3 CO Biomass

Stoker/Slope

dGrate/Other 1.64E+02 27 NO

WVJELDWENCraigsvi

lle

Wood Fired 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 1.82E+02 28 NO
Table 10: D/F Total Mass Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design

Total Mass 

PCDD/PCDF 

Unit ng/dscm @3%O2 Rank

In top 12 

pct?

ORFlakeboar

dEugene Boiler-2 Biomass

Dutch 

Oven/Susp. 

Burner

ng/dscm @ 

7% O2 1.63E-01 1 YES

ORRosboroS

pringfield DV 01.1 Biomass

Dutch 

Oven/Susp. 

Burner

ng/dscm @ 

7% O2 9.12E+00 2 NO

WAGraysHar

borPaper

No. 6 Boiler 

(EU2) Biomass

Dutch 

Oven/Susp. 

Burner

ng/dscm @ 

7% O2 1.71E+01 3 NO

ORGeorgiaP

acificWauna

Mill

EU35 - 

Fluidized 

Bed Boiler Biomass FB

ng/dscm @ 

7% O2 3.00E-02 1 YES

ALIPCourtlan

d

No. 3 

Combination 

Boier / 

11Cu301 Biomass FB

ng/dscm @ 

7% O2 1.09E-01 2 YES

NDCargillWe

stFargo

Foster 

Wheeler 

Boiler 

(EU43) Biomass FB

ng/dscm @ 

7% O2 1.83E-01 3 YES

TNBowaterN

ewsprint

Bubbling 

Fluidized 

Bed Boiler Biomass FB

ng/dscm @ 

7% O2 1.90E-01 4 YES

GATempleInl

andRome WF Biomass FB

ng/dscm @ 

7% O2 5.59E-01 5 YES

TNDomtar23

84 HFB1-1 Biomass FB

ng/dscm @ 

7% O2 1.45E+00 6 NO

ARWeyerhae

userDierksMi

ll SN-45 Biomass Fuel Cell

ng/dscm @ 

7% O2 1.79E-02 1 YES

WAWeyerha

euser_Raym

ond

Hog Fuel 

Boiler EU1 Biomass Fuel Cell

ng/dscm @ 

7% O2 3.19E-02 2 YES

MSWeyerha

euserBruce

AA-002 No. 

2 Boiler Biomass Fuel Cell

ng/dscm @ 

7% O2 1.67E-01 3 YES

ORWeyerha

euserCoWarr

entonLumber

Mill 3-HFB Biomass Fuel Cell

ng/dscm @ 

7% O2 3.07E-01 4 YES

ARAnthonyF

orestProduct

s SN-12 Biomass Fuel Cell

ng/dscm @ 

7% O2 5.65E-01 5 YES

MTPlumCree

k

Wellons 

Plywood Biomass Fuel Cell

ng/dscm @ 

7% O2 1.17E+00 6 NO

IDPotlatch PB-1 CE Biomass Fuel Cell

ng/dscm @ 

7% O2 3.43E+00 7 NO

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design
Table 10: D/F Total Mass Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design

Total Mass 

PCDD/PCDF 

Unit ng/dscm @3%O2 Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

GAGPMadis

onPly

800 Wood 

Waste Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 2.93E-02 1 YES

SCMarlboroP

aper

Hogged Fuel 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 3.99E-02 2 YES

ARPotlatchF

orestWarren

Wellons 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 5.84E-02 3 NO

MEBoralexSt

ratton Boiler #1 Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 9.06E-02 4 NO

MESDWarre

nSomerset

No2 Power 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.89E-01 5 NO

KYNewPageWickliffe B09 BiomassStoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 2.02E-01 6 NO

ALBoiseWhit

ePaperJacks

on

102-0001-

Z013 Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 3.02E-01 8 NO

WANipponP

aper

#8 Hog Fuel 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 3.18E-01 9 NO

SCInternatio

nalPaperEas

tover

No. 2 Power 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 4.11E-01 10 NO

MTSmurfitSt

one

Multi-Fuel 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 4.58E-01 11 NO

SCBowaterC

oatedPaper

Combination 

Boiler No. 2 Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 6.57E-01 12 NO

ARGBPMorri

lton SN-04 Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.76E+00 13 NO

GAGPCellulo

seBrunswick

U700 -- No. 

4 Power 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.90E+00 14 NO

WAKimberly

ClarkEverett

No. 14 

Cogeneration 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 2.70E+00 15 NO

PAProctorGa

mbleMehoop

anyPA

Boiler #3 

(033A) Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 3.23E+00 16 NO

ALMeadwest

vacoCottonto

n46

No.1 Wood 

Residue 

Boiler Biomass

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 3.85E+01 17 NO
Table 10: D/F Total Mass Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design

Total Mass 

PCDD/PCDF 

Unit ng/dscm @3%O2 Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

INPurdueUni

verisity Boiler 5 Coal FB

ng/dscm @ 

7% O2 1.91E-03 1 YES

IARoquetteA

merica

Circulating 

Fluidized 

Bed Boiler 

(121) Coal FB

ng/dscm @ 

7% O2 1.66E-02 2 YES

GASPNewsp

rint PB2 Coal FB

ng/dscm @ 

7% O2 8.39E-02 3 NO

IAUofIowa

EP7 Boiler 

11 Coal FB

ng/dscm @ 

7% O2 9.59E-02 4 NO

IAADMCorn

ProcessingC

R EU-501B Coal FB

ng/dscm @ 

7% O2 9.77E-02 5 NO

ILPolyOne B1 Coal FB

ng/dscm @ 

7% O2 1.50E-01 6 NO

MENewPageRumford

Cogen#6 & 

#7 Coal FB

ng/dscm @ 

7% O2 1.65E-01 7 NO

IAArchersDa

nielsMidland

DesMoines

Asea Boiler 

#1 Coal FB

ng/dscm @ 

7% O2 2.37E-01 8 NO

SCSonocoH

artsville

Boiler 

Number 9 Coal FB

ng/dscm @ 

7% O2 2.59E-01 9 NO

ILBungeDan

ville CFB Boiler Coal FB

ng/dscm @ 

7% O2 3.42E-01 10 NO

PAPHGlatfelt

er PB5 Coal FB

ng/dscm @ 

7% O2 5.20E-01 11 NO

NCUNCCoge

n ES-001 Coal FB

ng/dscm @ 

7% O2 2.06E+00 12 NO

WVPPGMart

insville

R011-Boiler 

3 Coal PC

ng/dscm @ 

7% O2 1.82E-02 1 YES

NCMillerCoor

s

ES-2 

Coal/No. 2 & 

6 Fuel Oil 

Boiler Coal PC

ng/dscm @ 

7% O2 1.91E-02 2 YES

GAGPCedar

Springs

U500 - 

Power Boiler 

No 1 Coal PC

ng/dscm @ 

7% O2 3.45E-02 3 NO

INTateLyleS

agamore 31B1 Coal PC

ng/dscm @ 

7% O2 4.80E-02 4 NO
Table 10: D/F Total Mass Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design

Total Mass 

PCDD/PCDF 

Unit ng/dscm @3%O2 Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

VASmurfitSt

oneWestpt PB08 Coal PC

ng/dscm @ 

7% O2 1.59E-01 5 NO

SCCogenSo

uth

B001 - Main 

Boiler Coal PC

ng/dscm @ 

7% O2 2.44E-01 6 NO

TNEastman_

NO_CBIDAT

A Boiler 30 Coal PC

ng/dscm @ 

7% O2 2.70E-01 7 NO

MITBSimonP

owerPlant Unit 1 Coal PC

ng/dscm @ 

7% O2 6.21E-01 8 NO

IAUofNorther

nIowa Boiler #3 Coal PC

ng/dscm @ 

7% O2 9.00E-01 9 NO

VAINVISTA

Waynesboro

2-205 (B#2) 

Boiler #2 Coal PC

ng/dscm @ 

7% O2 2.31E+00 10 NO

KYISPChemi

cals 0AA (Riley) Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 2.53E-03 1 YES

WINewPage

Biron B24 Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.24E-02 2 YES

ILAbbottAbb

ottPark Unit 5AP Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.51E-02 3 NO

IAMonsanto

Muscatine

Boiler #8 (EP195) Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 4.16E-02 4 NO

INNotreDam

e B-4 Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 4.93E-02 5 NO

TNCargillMe

mphis

Stoker Boiler 

8001 Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 5.05E-02 6 NO

NCDomtar

65-25-0310 

(No. 2 Hog 

Fuel Boiler) Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 9.00E-02 7 NO

WVATKRock

etCenter

NB2766 W17479-W 

(Boiler 17) Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 9.69E-02 8 NO

NCBlueRidg

ePaper G11042 Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.91E-01 9 NO

WIThilmanyL

LC

B09 and B11 

(common 

stack) Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 2.26E-01 10 NO
Table 10: D/F Total Mass Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design

Total Mass 

PCDD/PCDF 

Unit ng/dscm @3%O2 Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

OHMortonSa

ltRittman

B002 - CoalFired Boiler 

#2 Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 2.41E-01 11 NO

PAAppletonP

apers #036 Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.48E+00 12 NO

MNVersoPap

er EU006 B&W Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 1.88E+00 13 NO

VAUniversity

ofVirginia 7103-1-01R Coal

Stoker/Slope

dGrate/Other

ng/dscm @ 

7% O2 3.75E+00 14 NO
Table 11: D/F TEQ Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design ng/dscm @3%O2

CountOfTEQ 

PCDD/PCDF Rank

In top 12 

pct?

ORFlakeboar

dEugene Boiler-2 Biomass

Dutch 

Oven/Susp. 

Burner 9.52E-03 3 1 YES

ORRosboroS

pringfield DV 01.1 Biomass

Dutch 

Oven/Susp. 

Burner 9.53E-02 3 2 NO

WAGraysHar

borPaper

No. 6 Boiler 

(EU2) Biomass

Dutch 

Oven/Susp. 

Burner 3.67E-01 3 3 NO

ORGeorgiaP

acificWauna

Mill

EU35 - 

Fluidized 

Bed Boiler Biomass FB 2.27E-03 3 1 YES

ALIPCourtlan

d

No. 3 

Combination 

Boier / 

11Cu301 Biomass FB 3.27E-03 3 2 YES

TNBowaterN

ewsprint

Bubbling 

Fluidized 

Bed Boiler Biomass FB 5.30E-03 3 3 YES

GATempleInl

andRome WF Biomass FB 9.45E-03 3 4 YES

NDCargillWe

stFargo

Foster 

Wheeler 

Boiler 

(EU43) Biomass FB 1.09E-02 3 5 YES

TNDomtar23

84 HFB1-1 Biomass FB 1.85E-02 3 6 NO

WAWeyerha

euser_Raym

ond

Hog Fuel 

Boiler EU1 Biomass Fuel Cell 2.42E-04 3 7 NO

MSWeyerha

euserBruce

AA-002 No. 

2 Boiler Biomass Fuel Cell 3.35E-03 3 8 NO

ORWeyerha

euserCoWarr

entonLumber

Mill 3-HFB Biomass Fuel Cell 4.46E-03 1 9 NO

ARWeyerhae

userDierksMi

ll SN-45 Biomass Fuel Cell 8.48E-03 3 10 NO

ARAnthonyF

orestProduct

s SN-12 Biomass Fuel Cell 1.03E-02 3 11 NO

MTPlumCree

k

Wellons 

Plywood Biomass Fuel Cell 2.32E-02 3 12 NO

IDPotlatch PB-1 CE Biomass Fuel Cell 1.70E+00 3 13 NO

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design
Table 11: D/F TEQ Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design ng/dscm @3%O2

CountOfTEQ 

PCDD/PCDF Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

ARGBPMorri

lton SN-04 Biomass

Stoker/Slope

dGrate/Other 1.52E-05 3 1 YES

MEBoralexSt

ratton Boiler #1 Biomass

Stoker/Slope

dGrate/Other 1.62E-03 3 2 YES

GAGPMadis

onPly

800 Wood 

Waste Boiler Biomass

Stoker/Slope

dGrate/Other 2.01E-03 3 3 NO

SCMarlboroP

aper

Hogged Fuel 

Boiler Biomass

Stoker/Slope

dGrate/Other 2.59E-03 3 4 NO

WANipponP

aper

#8 Hog Fuel 

Boiler Biomass

Stoker/Slope

dGrate/Other 6.06E-03 3 6 NO

ALBoiseWhit

ePaperJacks

on

102-0001-

Z013 Biomass

Stoker/Slope

dGrate/Other 9.29E-03 3 7 NO

KYNewPageWickliffe B09 BiomassStoker/Slope

dGrate/Other 1.00E-02 3 8 NO

SCInternatio

nalPaperEas

tover

No. 2 Power 

Boiler Biomass

Stoker/Slope

dGrate/Other 1.03E-02 3 9 NO

ARPotlatchF

orestWarren

Wellons 

Boiler Biomass

Stoker/Slope

dGrate/Other 1.06E-02 3 10 NO

SCBowaterC

oatedPaper

Combination 

Boiler No. 2 Biomass

Stoker/Slope

dGrate/Other 1.44E-02 3 11 NO

WAKimberly

ClarkEverett

No. 14 

Cogeneration 

Boiler Biomass

Stoker/Slope

dGrate/Other 2.06E-02 3 12 NO

MTSmurfitSt

one

Multi-Fuel 

Boiler Biomass

Stoker/Slope

dGrate/Other 2.12E-02 3 13 NO

MESDWarre

nSomerset

No2 Power 

Boiler Biomass

Stoker/Slope

dGrate/Other 2.59E-02 3 14 NO

GAGPCellulo

seBrunswick

U700 -- No. 

4 Power 

Boiler Biomass

Stoker/Slope

dGrate/Other 2.59E-02 3 15 NO

ALMeadwest

vacoCottonto

n46

No.1 Wood 

Residue 

Boiler Biomass

Stoker/Slope

dGrate/Other 3.08E-02 3 16 NO

PAProctorGa

mbleMehoop

anyPA

Boiler #3 

(033A) Biomass

Stoker/Slope

dGrate/Other 3.44E-02 3 17 NO
Table 11: D/F TEQ Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design ng/dscm @3%O2

CountOfTEQ 

PCDD/PCDF Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

SCSonocoH

artsville

Boiler 

Number 9 Coal FB 9.05E-06 3 1 YES

INPurdueUni

verisity Boiler 5 Coal FB 9.33E-04 3 2 YES

IARoquetteA

merica

Circulating 

Fluidized 

Bed Boiler 

(121) Coal FB 1.10E-03 3 3 NO

IAArchersDa

nielsMidland

DesMoines

Asea Boiler 

#1 Coal FB 3.13E-03 3 4 NO

IAUofIowa

EP7 Boiler 

11 Coal FB 3.56E-03 3 5 NO

MENewPageRumford

Cogen#6 & 

#7 Coal FB 6.04E-03 3 6 NO

GASPNewsp

rint PB2 Coal FB 7.36E-03 3 7 NO

ILPolyOne B1 Coal FB 7.37E-03 3 8 NO

PAPHGlatfelt

er PB5 Coal FB 9.38E-03 3 9 NO

IAADMCorn

ProcessingC

R EU-501B Coal FB 1.30E-02 3 10 NO

ILBungeDan

ville CFB Boiler Coal FB 1.57E-02 3 11 NO

NCUNCCoge

n ES-001 Coal FB 3.42E-02 3 12 NO

GAGPCedar

Springs

U500 - 

Power Boiler 

No 1 Coal PC 1.04E-03 3 1 YES

WVPPGMart

insville

R011-Boiler 

3 Coal PC 2.12E-03 3 2 YES

NCMillerCoor

s

ES-2 

Coal/No. 2 & 

6 Fuel Oil 

Boiler Coal PC 2.43E-03 3 3 NO

VASmurfitSt

oneWestpt PB08 Coal PC 3.25E-03 3 4 NO
Table 11: D/F TEQ Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design ng/dscm @3%O2

CountOfTEQ 

PCDD/PCDF Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

INTateLyleS

agamore 31B1 Coal PC 5.42E-03 3 5 NO

TNEastman_

NO_CBIDAT

A Boiler 30 Coal PC 6.55E-03 3 6 NO

IAUofNorther

nIowa Boiler #3 Coal PC 2.02E-02 3 7 NO

SCCogenSo

uth

B001 - Main 

Boiler Coal PC 2.73E-02 3 8 NO

MITBSimonP

owerPlant Unit 1 Coal PC 4.59E-02 3 9 NO

VAINVISTA

Waynesboro

2-205 (B#2) 

Boiler #2 Coal PC 1.21E-01 3 10 NO

WINewPage

Biron B24 Coal

Stoker/Slope

dGrate/Other 1.52E-03 3 1 YES

ILAbbottAbb

ottPark Unit 5AP Coal

Stoker/Slope

dGrate/Other 2.13E-03 3 2 YES

NCDomtar

65-25-0310 

(No. 2 Hog 

Fuel Boiler) Coal

Stoker/Slope

dGrate/Other 2.75E-03 3 3 NO

KYISPChemi

cals 0AA (Riley) Coal

Stoker/Slope

dGrate/Other 2.85E-03 3 4 NO

WVATKRock

etCenter

NB2766 W17479-W 

(Boiler 17) Coal

Stoker/Slope

dGrate/Other 2.87E-03 3 5 NO

TNCargillMe

mphis

Stoker Boiler 

8001 Coal

Stoker/Slope

dGrate/Other 3.45E-03 3 6 NO

NCBlueRidg

ePaper G11042 Coal

Stoker/Slope

dGrate/Other 3.68E-03 3 7 NO

IAMonsanto

Muscatine

Boiler #8 (EP195) Coal

Stoker/Slope

dGrate/Other 4.11E-03 3 8 NO

OHMortonSa

ltRittman

B002 - CoalFired Boiler 

#2 Coal

Stoker/Slope

dGrate/Other 4.94E-03 3 9 NO

INNotreDam

e B-4 Coal

Stoker/Slope

dGrate/Other 7.18E-03 3 10 NO
Table 11: D/F TEQ Floor by Combustor

FacilityID

CombustorID

_common

MACT Floor 

FuelCat

Combustor 

Design ng/dscm @3%O2

CountOfTEQ 

PCDD/PCDF Rank

In top 12 

pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

WIThilmanyL

LC

B09 and B11 

(common 

stack) Coal

Stoker/Slope

dGrate/Other 8.68E-03 3 11 NO

PAAppletonP

apers #036 Coal

Stoker/Slope

dGrate/Other 2.00E-02 3 12 NO

VAUniversity

ofVirginia 7103-1-01R Coal

Stoker/Slope

dGrate/Other 3.55E-02 3 13 NO

MNVersoPap

er EU006 B&W Coal

Stoker/Slope

dGrate/Other 1.10E-01 3 14 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

MSWeyerha

euserColumb

us AA-012 CO Biomass

Stoker/Slope

dGrate/Other 1.84E+02 29 NO

MSIPVicksbu

rg

Power BoilerAA-006 CO BiomassStoker/Slope

dGrate/Other 1.97E+02 30 NO

ARDelticTim

berWaldo

Wood Fired 

Boiler No. 1 

(SN-13) CO Biomass

Stoker/Slope

dGrate/Other 1.99E+02 31 NO

MNDESPHa

nsONyman EU007 CO Biomass

Stoker/Slope

dGrate/Other 2.04E+02 32 NO

WIAlgoma B03 CO Biomass

Stoker/Slope

dGrate/Other 2.07E+02 33 NO

GAGPCellulo

seBrunswick

U700 -- No. 

4 Power 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.17E+02 34 NO

GAADMLoca

tion551

B115ANorth Hurst CO BiomassStoker/Slope

dGrate/Other 2.28E+02 35 NO

SCInternatio

nalPaperEas

tover

No. 2 Power 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.32E+02 36 NO

TXAnthonyF

orestProdATLEP 11.1 

Hurst CO Biomass

Stoker/Slope

dGrate/Other 2.33E+02 37 NO

ARLeolaLum

berMill SN-01A CO Biomass

Stoker/Slope

dGrate/Other 2.38E+02 38 NO

SCMarlboroP

aper

Hogged Fuel 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.49E+02 39 NO

ALBoiseWhit

ePaperJacks

on

102-0001-

Z013 CO Biomass

Stoker/Slope

dGrate/Other 2.49E+02 40 NO

ALMeadwest

vacoCottonto

n46

No.2 Wood 

Residue 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.60E+02 41 NO

ARDelticTim

berWaldo

Wood Fired 

Boiler No. 2 

(SN-14) CO Biomass

Stoker/Slope

dGrate/Other 2.67E+02 42 NO

GARayonier

Baxley PB02 CO Biomass

Stoker/Slope

dGrate/Other 2.68E+02 43 NO

GAADMLoca

tion551

B115B-South 

Hurst CO Biomass

Stoker/Slope

dGrate/Other 2.70E+02 44 NO

OHSmurfitCo

shocton B006 CO Biomass

Stoker/Slope

dGrate/Other 2.73E+02 45 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

ARPotlatchF

orestWarren

Wellons 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.86E+02 46 NO

ARGBPMorri

lton SN-04 CO Biomass

Stoker/Slope

dGrate/Other 2.95E+02 47 NO

WAGPCama

s

No. 3 Power 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.96E+02 48 NO

ORJeldWen

KlamanthFall

s BLRG CO Biomass

Stoker/Slope

dGrate/Other 2.97E+02 49 NO

TXAnthonyF

orestProdATLEP 10.1 

Superior CO Biomass

Stoker/Slope

dGrate/Other 3.00E+02 50 NO

FLGPPalatka EU16 CO Biomass

Stoker/Slope

dGrate/Other 3.01E+02 51 NO

WIFlambeau

RiverPaper B24 CO Biomass

Stoker/Slope

dGrate/Other 3.07E+02 52 NO

ARGPGurdo

nPlyLumber

SN-01 No. 1 

Wood 

Residue 

Fired Boiler CO Biomass

Stoker/Slope

dGrate/Other 3.21E+02 53 NO

ARGPGurdo

nPlyLumber

SN-02 No. 2 

Wood 

Residue 

Fired Boiler CO Biomass

Stoker/Slope

dGrate/Other 3.39E+02 54 NO

LAGPLogans

portPly EQT-0009 CO Biomass

Stoker/Slope

dGrate/Other 3.43E+02 55 NO

GARayonierJ

esupMill PB03 CO Biomass

Stoker/Slope

dGrate/Other 3.48E+02 56 NO

FLCFRC252

Boiler #3 

(McBurney) CO Biomass

Stoker/Slope

dGrate/Other 3.64E+02 57 NO

LAWeyerhae

user1043 EQT - 0010 CO Biomass

Stoker/Slope

dGrate/Other 3.76E+02 58 NO

GAP&GAlba

ny B002 CO Biomass

Stoker/Slope

dGrate/Other 3.84E+02 59 NO

TXGPClevel

andPlyLumb

er GRP-SBOIL CO Biomass

Stoker/Slope

dGrate/Other 3.87E+02 60 NO

FLSmurfitStone 5PB CO BiomassStoker/Slope

dGrate/Other 3.88E+02 61 NO

ARLeolaLum

berMill SN-01B CO Biomass

Stoker/Slope

dGrate/Other 3.92E+02 62 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

MSBowaterS

outh Bark Boiler CO Biomass

Stoker/Slope

dGrate/Other 4.13E+02 63 NO

ALWestervel

t

Wellons - 

Unit 001 CO Biomass

Stoker/Slope

dGrate/Other 4.33E+02 64 NO

LAWeyerhae

userDodson ES-017 WFB CO Biomass

Stoker/Slope

dGrate/Other 4.33E+02 65 NO

MEBoralexSt

ratton Boiler #1 CO Biomass

Stoker/Slope

dGrate/Other 4.36E+02 66 NO

IDPotlatch PB-2 Riley CO Biomass

Stoker/Slope

dGrate/Other 4.55E+02 67 NO

ARWestFras

erHuttig SN-01 CO Biomass

Stoker/Slope

dGrate/Other 4.75E+02 68 NO

MSSanderso

nPlumbing AD-001 CO Biomass

Stoker/Slope

dGrate/Other 4.76E+02 69 NO

WANipponP

aper

#8 Hog Fuel 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 4.98E+02 70 NO

AREvergreen

Packaging BB CO Biomass

Stoker/Slope

dGrate/Other 5.03E+02 71 NO

WIAshland B20 CO Biomass

Stoker/Slope

dGrate/Other 5.11E+02 72 NO

MSGPBaySp

rings

AA-001 

(Boiler No. 1) CO Biomass

Stoker/Slope

dGrate/Other 5.46E+02 73 NO

OKPanPacifi

cProducts EU 100 CO Biomass

Stoker/Slope

dGrate/Other 5.57E+02 74 NO

TXwestfraser Boiler-1 CO Biomass

Stoker/Slope

dGrate/Other 5.70E+02 75 NO

LAHuntPollo

ck EQT0005 CO Biomass

Stoker/Slope

dGrate/Other 5.85E+02 76 NO

MSGPBaySp

rings

AA-003 

(Boiler No. 2) CO Biomass

Stoker/Slope

dGrate/Other 5.86E+02 77 NO

ARDelticTim

berOla

Wood Fired 

Boiler at Ola 

Mill (SN-13) CO Biomass

Stoker/Slope

dGrate/Other 6.20E+02 79 NO

WILPHaywar

d

K2 Line 1 

Konus CO Biomass

Stoker/Slope

dGrate/Other 7.43E+02 80 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

TXMeadWes

tvacoEvadal

e 21-2105 CO Biomass

Stoker/Slope

dGrate/Other 7.48E+02 81 NO

ARWeyerhae

userDierksMi

ll SN-32 CO Biomass

Stoker/Slope

dGrate/Other 8.21E+02 82 NO

MEVersoPap

erAndroscog

gin WFI CO Biomass

Stoker/Slope

dGrate/Other 8.54E+02 83 NO

ALGPEngine

eredWoodPr

oductsThorn

sby

EU 001 

Wood Fired 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 8.75E+02 84 NO

ARGBPMorri

lton SN-02 CO Biomass

Stoker/Slope

dGrate/Other 1.07E+03 85 NO

TXTempleInl

andFiberboar

d FB-25 CO Biomass

Stoker/Slope

dGrate/Other 1.09E+03 86 NO

WILPHaywar

d

K1 Line 1 

Konus CO Biomass

Stoker/Slope

dGrate/Other 1.20E+03 87 NO

LAHoodIndu

stries

EQT001 

(wood-fired 

boiler No. 1) CO Biomass

Stoker/Slope

dGrate/Other 1.21E+03 88 NO

LAGPPortHu

dson

EQT0099 - 

Combination 

Boiler No. 1 CO Biomass

Stoker/Slope

dGrate/Other 1.26E+03 89 NO

IDRileyCreek

Lumber HFB2 CO Biomass

Stoker/Slope

dGrate/Other 1.31E+03 90 NO

ALManningto

nWoodFloors BB01 CO Biomass

Stoker/Slope

dGrate/Other 1.31E+03 91 NO

ALManningto

nWoodFloors BB02 CO Biomass

Stoker/Slope

dGrate/Other 1.31E+03 92 NO

LABoiseCas

cadeOakdale B-1 CO Biomass

Stoker/Slope

dGrate/Other 1.45E+03 93 NO

LAHuntNatal

bany EQT0001 CO Biomass

Stoker/Slope

dGrate/Other 1.57E+03 94 NO

LAWestFras

erJoyce 74A CO Biomass

Stoker/Slope

dGrate/Other 1.61E+03 95 NO

NCDomtar

64-25-0290 

(No. 1 Hog 

Fuel Boiler) CO Biomass

Stoker/Slope

dGrate/Other 1.63E+03 96 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

WILPHaywar

d

K4 Line 2 

Konus CO Biomass

Stoker/Slope

dGrate/Other 1.65E+03 97 NO

LAWestFras

erJoyce 75A CO Biomass

Stoker/Slope

dGrate/Other 1.74E+03 98 NO

IDMoyieSprin

gs 

Lumber420 HFB1 CO Biomass

Stoker/Slope

dGrate/Other 1.88E+03 99 NO

MSWeyerha

euserBruce

AA-001 No. 

1 Boiler CO Biomass

Stoker/Slope

dGrate/Other 1.95E+03 100 NO

LAHoodIndu

stries

EQT002 

(wood-fired 

boiler No. 2) CO Biomass

Stoker/Slope

dGrate/Other 2.33E+03 101 NO

LAWestFras

erJoyce 74B CO Biomass

Stoker/Slope

dGrate/Other 2.33E+03 102 NO

WILPHaywar

d

K3 Line 2 

Konus CO Biomass

Stoker/Slope

dGrate/Other 2.35E+03 103 NO

PACraftMast

er

No2 Boiler 

Source ID 

032 CO Biomass

Stoker/Slope

dGrate/Other 2.40E+03 104 NO

GAGPMadis

onPly

800 Wood 

Waste Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.48E+03 105 NO

ALMeadwest

vacoCottonto

n46

No.1 Wood 

Residue 

Boiler CO Biomass

Stoker/Slope

dGrate/Other 2.73E+03 106 NO

SCBowaterC

oatedPaper

Combination 

Boiler No. 2 CO Biomass

Stoker/Slope

dGrate/Other 2.82E+03 107 NO

MSWeyerha

euser1398 Boiler No. 1 CO Biomass

Stoker/Slope

dGrate/Other 2.89E+03 108 NO

HIPuuneneS

ugarMill Boiler 3 CO Biomass

Stoker/Slope

dGrate/Other 3.07E+03 109 NO

GAPCAVald

osta 1005 CO Biomass

Stoker/Slope

dGrate/Other 3.42E+03 110 NO

GAPCAVald

osta 1006 CO Biomass

Stoker/Slope

dGrate/Other 3.42E+03 111 NO

LAHuntPollo

ck EQT0017 CO Biomass

Stoker/Slope

dGrate/Other 3.57E+03 112 NO

HIPuuneneS

ugarMill Boiler 1 CO Biomass

Stoker/Slope

dGrate/Other 3.75E+03 113 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

HIPuuneneS

ugarMill Boiler 2 CO Biomass

Stoker/Slope

dGrate/Other 3.75E+03 114 NO

ORBBSMMe

dford B1 CO Biomass

Stoker/Slope

dGrate/Other 3.85E+03 115 NO

ORBBSMMe

dford B2 CO Biomass

Stoker/Slope

dGrate/Other 3.85E+03 116 NO

ORBBSMMe

dford B3 CO Biomass

Stoker/Slope

dGrate/Other 3.85E+03 117 NO

WABoiseKett

leFallsPlywo

od B1 CO Biomass

Stoker/Slope

dGrate/Other 5.48E+03 118 NO

GAWestFras

erFolkston FOB1 CO Biomass

Stoker/Slope

dGrate/Other 9.46E+03 119 NO

GAWestFras

erFolkston FOB2 CO Biomass

Stoker/Slope

dGrate/Other 1.33E+04 120 NO

IAADMCorn

ProcessingC

R EU-530 CO Coal FB 8.26E+00 1 YES

MENewPageRumford Cogen#6 CO Coal FB 1.46E+01 2 YES

MENewPageRumford Cogen#7 CO Coal FB 1.46E+01 3 YES

IAADMCorn

ProcessingC

R EU-501B CO Coal FB 1.84E+01 4 NO

IAADMCorn

ProcessingC

R EU-502A CO Coal FB 2.16E+01 5 NO

PAPHGlatfelt

er PB5 CO Coal FB 2.32E+01 6 NO

IAADMCorn

ProcessingC

R EU-501A CO Coal FB 3.00E+01 7 NO

INPurdueUni

verisity Boiler 5 CO Coal FB 3.05E+01 8 NO

ILPolyOne B1 CO Coal FB 3.86E+01 9 NO

NCUNCCoge

n ES-001 CO Coal FB 4.11E+01 10 NO

NEADMLinc

oln

EU26 Coal 

Boiler CO Coal FB 4.31E+01 11 NO

ILBungeDan

ville CFB Boiler CO Coal FB 4.90E+01 12 NO

IAADMCorn

ProcessingC

R EU-502B CO Coal FB 5.01E+01 13 NO

IAUofIowa

EP7 Boiler 

11 CO Coal FB 5.07E+01 14 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

IAArchersDa

nielsMidland

DesMoines

Asea Boiler 

#1 CO Coal FB 5.52E+01 15 NO

GASPNewsp

rint PB2 CO Coal FB 1.18E+02 16 NO

SCSonocoH

artsville

Boiler 

Number 9 CO Coal FB 1.68E+02 17 NO

ILDukeEnerg

yTuscola Unit 3 CO Coal PC 5.53E-02 1 YES

ILDukeEnerg

yTuscola Unit 4 CO Coal PC 5.53E-02 2 YES

ILDukeEnerg

yTuscola Unit 1 CO Coal PC 5.71E-02 3 YES

VAPhilipMorr

isPark500 B2 CO Coal PC 1.36E+00 4 YES

AZCatalystP

aperSnowfla

ke

Power Boiler 

#2 Coal CO Coal PC 2.23E+00 5 YES

OKGPMusko

geeMill B-3 CO Coal PC 3.20E+00 6 NO

ILPrairiePow

erPearl B1 CO Coal PC 6.84E+00 7 NO

INTateLyleS

agamore 31B1 CO Coal PC 6.85E+00 8 NO

VAPhilipMorr

isPark500 B3 CO Coal PC 8.82E+00 9 NO

IAUofNorther

nIowa Boiler #3 CO Coal PC 1.03E+01 10 NO

TNDuPontOl

dHickoryPlan

t #20 Boiler CO Coal PC 1.08E+01 11 NO

INNewEnerg

y Riley Boiler CO Coal PC 1.21E+01 12 NO

INNewEnferg

y Riley Boiler CO Coal PC 1.24E+01 13 NO

NCBlueRidg

ePaper G11040 CO Coal PC 1.35E+01 14 NO

OKGPMusko

geeMill B-4 CO Coal PC 1.40E+01 15 NO

INAlcoaWarri

ck Unit #3 CO Coal PC 1.41E+01 16 NO

FLSmurfitStone 7PB CO Coal PC 1.53E+01 17 NO

NCBlueRidg

ePaper G11039 CO Coal PC 1.53E+01 18 NO

NCBlueRidg

ePaper G11038 CO Coal PC 1.58E+01 19 NO

SCCogenSo

uth

B001 - Main 

Boiler CO Coal PC 1.61E+01 20 NO

VASmurfitSt

oneWestpt PB08 CO Coal PC 1.65E+01 21 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

TNEastman_

NO_CBIDAT

A Boiler 30 CO Coal PC 1.78E+01 22 NO

NCMillerCoor

s

ES-2 

Coal/No. 2 & 

6 Fuel Oil 

Boiler CO Coal PC 1.80E+01 23 NO

IDTASCOPa

ul

Erie City 

Boiler CO Coal PC 1.93E+01 24 NO

VAPhilipMorr

isMC PC CO Coal PC 2.01E+01 25 NO

WYFMCGre

enRiver NS-1A CO Coal PC 2.14E+01 26 NO

SCInternatio

nalPaperEas

tover

No. 1 Power 

Boiler CO Coal PC 2.57E+01 27 NO

OKGPMusko

geeMill B-2 CO Coal PC 2.65E+01 28 NO

WYGeneralC

hemical

GR-2-L (C 

BOILER) CO Coal PC 3.03E+01 29 NO

VAGPBigIsla

nd2703

PWR04 - No. 

4 Power 

Boiler CO Coal PC 3.36E+01 30 NO

VAINVISTA

Waynesboro

2-205 (B#2) 

Boiler #2 CO Coal PC 4.13E+01 31 NO

INAlcoaWarri

ck Unit #2 CO Coal PC 4.30E+01 32 NO

PADomtarJo

hnsonburg

#81 Coal 

Boiler CO Coal PC 6.83E+01 33 NO

PADomtarJo

hnsonburg

#82 Coal 

Boiler CO Coal PC 6.83E+01 34 NO

NCBlueRidg

ePaper G11037 CO Coal PC 7.52E+01 35 NO

MITBSimonP

owerPlant Unit 1 CO Coal PC 7.87E+01 36 NO

MOAnheuser

Busch Boiler 5 CO Coal PC 1.09E+02 37 NO

WVPPGMart

insville

R011-Boiler 

3 CO Coal PC 1.30E+02 38 NO

MDNewPageLuke No. 25 CO Coal PC 1.31E+02 39 NO

MOAnheuser

Busch Boiler 1 CO Coal PC 1.39E+02 40 NO

ALIPCourtlan

d

No.2 

Combination 

Boiler / 

11CU201 CO Coal PC 1.70E+02 41 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

INNotreDam

e B-4 CO Coal

Stoker/Slope

dGrate/Other 4.29E+00 1 YES

OHMortonSa

ltRittman

B002 - CoalFired Boiler 

#2 CO Coal

Stoker/Slope

dGrate/Other 1.47E+01 2 YES

WVDuPontW

ashingtonWo

rks P05 CO Coal

Stoker/Slope

dGrate/Other 1.63E+01 3 YES

OHAppletonI

deas

Boiler 4 

(B003) CO Coal

Stoker/Slope

dGrate/Other 1.97E+01 4 YES

OHAkronThe

rmalEnergy

Boiler #32 

(B001) CO Coal

Stoker/Slope

dGrate/Other 2.47E+01 5 YES

PABellefield

Plant Boiler 1 CO Coal

Stoker/Slope

dGrate/Other 2.55E+01 6 YES

NCNC_Duke

University_D

urham 7754-03 CO Coal

Stoker/Slope

dGrate/Other 2.76E+01 7 YES

HIPuuneneS

ugarMill Boiler 3 CO Coal

Stoker/Slope

dGrate/Other 3.81E+01 8 YES

PABellefield

Plant Boiler 5 CO Coal

Stoker/Slope

dGrate/Other 3.82E+01 9 NO

IAMuscatine

PowerandW

ater Unit 7 CO Coal

Stoker/Slope

dGrate/Other 4.24E+01 10 NO

VAUniversity

ofVirginia 7103-1-01R CO Coal

Stoker/Slope

dGrate/Other 4.40E+01 11 NO

OHAppletonI

deas

Boiler 2 

(B002) CO Coal

Stoker/Slope

dGrate/Other 4.56E+01 12 NO

PABayValley

FoodsPittsbu

rgh Boiler No. 3 CO Coal

Stoker/Slope

dGrate/Other 5.18E+01 13 NO

PABayValley

FoodsPittsbu

rgh Boiler No. 4 CO Coal

Stoker/Slope

dGrate/Other 5.18E+01 14 NO

KYISPChemi

cals 0AA (Riley) CO Coal

Stoker/Slope

dGrate/Other 5.21E+01 15 NO

ILAbbottAbb

ottPark Unit 5AP CO Coal

Stoker/Slope

dGrate/Other 5.42E+01 16 NO

NCDomtar

65-25-0310 

(No. 2 Hog 

Fuel Boiler) CO Coal

Stoker/Slope

dGrate/Other 5.59E+01 17 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

MNVersoPap

er EU006 B&W CO Coal

Stoker/Slope

dGrate/Other 5.97E+01 18 NO

WIThilmanyL

LC B09 CO Coal

Stoker/Slope

dGrate/Other 6.45E+01 19 NO

WIThilmanyL

LC B11 CO Coal

Stoker/Slope

dGrate/Other 6.45E+01 20 NO

IAMonsanto

Muscatine

Boiler #8 (EP195) CO Coal

Stoker/Slope

dGrate/Other 6.49E+01 21 NO

MOColumbia

PowerPlant Boiler Unit 6 CO Coal

Stoker/Slope

dGrate/Other 6.51E+01 22 NO

MOColumbia

PowerPlant Boiler Unit 7 CO Coal

Stoker/Slope

dGrate/Other 6.51E+01 23 NO

NCNC_Duke

University_D

urham 7754-02 CO Coal

Stoker/Slope

dGrate/Other 6.85E+01 24 NO

NCEPCORR

oxboro 1-B CO Coal

Stoker/Slope

dGrate/Other 6.92E+01 25 NO

NCEPCORR

oxboro 1-A CO Coal

Stoker/Slope

dGrate/Other 6.92E+01 26 NO

NCEPCORR

oxboro 1-C CO Coal

Stoker/Slope

dGrate/Other 6.92E+01 27 NO

VAUniversity

ofVirginia 7103-1-02R CO Coal

Stoker/Slope

dGrate/Other 7.29E+01 28 NO

PABellefield

Plant Boiler 3 CO Coal

Stoker/Slope

dGrate/Other 7.65E+01 29 NO

IAUofIowa

EP6 Boiler 

10 CO Coal

Stoker/Slope

dGrate/Other 8.96E+01 30 NO

WVATKRock

etCenter

NB2766 W17479-W 

(Boiler 17) CO Coal

Stoker/Slope

dGrate/Other 8.99E+01 31 NO

SCClemson 04-B04 CO Coal

Stoker/Slope

dGrate/Other 9.57E+01 32 NO

MSWeyerha

euserColumb

us AA-012 CO Coal

Stoker/Slope

dGrate/Other 9.62E+01 33 NO

OHBataviaTr

ansmissions

Boiler 2 

(B002) CO Coal

Stoker/Slope

dGrate/Other 1.04E+02 34 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

WIFlambeau

RiverPaper B24 CO Coal

Stoker/Slope

dGrate/Other 1.04E+02 35 NO

NDMinnDakF

armers

Babcock and 

Wilcox Boiler 

#5 CO Coal

Stoker/Slope

dGrate/Other 1.07E+02 36 NO

NCEPCORS

outhport 1-A Boiler CO Coal

Stoker/Slope

dGrate/Other 1.40E+02 37 NO

NCEPCORS

outhport 1-B Boiler CO Coal

Stoker/Slope

dGrate/Other 1.40E+02 38 NO

NCEPCORS

outhport 1-C Boiler CO Coal

Stoker/Slope

dGrate/Other 1.40E+02 39 NO

PABayValley

FoodsPittsbu

rgh Boiler No. 1 CO Coal

Stoker/Slope

dGrate/Other 1.44E+02 40 NO

PABayValley

FoodsPittsbu

rgh Boiler No. 2 CO Coal

Stoker/Slope

dGrate/Other 1.44E+02 41 NO

VAUniversity

ofVirginia 7103-1-05 CO Coal

Stoker/Slope

dGrate/Other 1.53E+02 42 NO

WYFMCGra

nger UIN-14 CO Coal

Stoker/Slope

dGrate/Other 1.60E+02 43 NO

WIThilmany

PapersNicole

tMill B23 CO Coal

Stoker/Slope

dGrate/Other 2.12E+02 44 NO

WIThilmany

PapersNicole

tMill B24 CO Coal

Stoker/Slope

dGrate/Other 2.12E+02 45 NO

WYFMCGra

nger UIN-15 CO Coal

Stoker/Slope

dGrate/Other 2.36E+02 46 NO

MNADMCorn

Division

Coal Boiler 

#1 EU049 CO Coal

Stoker/Slope

dGrate/Other 2.53E+02 47 NO

MNADMCorn

Division

Coal Boiler 

#2 EU050 CO Coal

Stoker/Slope

dGrate/Other 2.53E+02 48 NO

MDNewPageLuke No. 24 CO Coal

Stoker/Slope

dGrate/Other 2.91E+02 49 NO

OHCampbell

sSoupCo B001 CO Coal

Stoker/Slope

dGrate/Other 3.79E+02 50 NO

OHCampbell

sSoupCo B002 CO Coal

Stoker/Slope

dGrate/Other 3.79E+02 51 NO
Table 9: CO Floor by Combustor

FacilityID

CombustorID

_common

Pollutant_Na

me

MACT Floor 

FuelCat

Combustor 

Design ppm @ 3% O2 Rank

In top 

12 pct?

APPENDIX C-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to 

Combustor Design

TNCargillMe

mphis

Stoker Boiler 

8001 CO Coal

Stoker/Slope

dGrate/Other 5.54E+02 52 NO

IDTASCOPa

ul

Babcock and 

Wilcox 

(B&W) Boiler CO Coal

Stoker/Slope

dGrate/Other 5.77E+02 53 NO

NCBlueRidg

ePaper G11042 CO Coal

Stoker/Slope

dGrate/Other 6.67E+02 54 NO

MNBlandinP

aperEnergyC

tr #5 Boiler CO Coal

Stoker/Slope

dGrate/Other 8.37E+02 55 NO

MNBlandinP

aperEnergyC

tr #6 Boiler CO Coal

Stoker/Slope

dGrate/Other 8.37E+02 56 NO

PAAppletonP

apers #036 CO Coal

Stoker/Slope

dGrate/Other 1.07E+03 57 NO

MIMortonSalt

Manistee No. 6 Boiler CO Coal

Stoker/Slope

dGrate/Other 1.29E+03 58 NO

IACargillEdd

yville 1.001 CO Coal

Stoker/Slope

dGrate/Other 4.37E+03 59 NO

IACargillEdd

yville 1.002 CO Coal

Stoker/Slope

dGrate/Other 4.37E+03 60 NO

IACargillEdd

yville 1.039 CO Coal

Stoker/Slope

dGrate/Other 4.37E+03 61 NO
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/5/2009 2.00E-04 -8.52E+00

Natural gas/No. 6 Residual oil/Wood: Bark - - 87.56 - 0.32 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/5/2009 2.00E-04 -8.52E+00

Natural gas/No. 6 Residual oil/Wood: Bark - - 87.56 - 0.32 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 11/13/2007 5.00E-03 -5.30E+00

/Natural gas/No. 6 Residual oil/Wood: Bark/ - - 79.04 - 16.02 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/6/2009 9.00E-04 -7.01E+00

Natural gas/No. 6 Residual oil/Wood: Bark - - 87.56 - 0.32 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/6/2009 9.00E-04 -7.01E+00

Natural gas/No. 6 Residual oil/Wood: Bark - - 87.56 - 0.32 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 11/13/2007 4.10E-03 -5.50E+00

/Natural gas/No. 6 Residual oil/Wood: Bark/ - - 79.04 - 16.02 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/6/2009 5.00E-04 -7.60E+00

Natural gas/No. 6 Residual oil/Wood: Bark - - 87.56 - 0.32 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/6/2009 5.00E-04 -7.60E+00

Natural gas/No. 6 Residual oil/Wood: Bark - - 87.56 - 0.32 

 

YES Biomass 1 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 11/13/2007 7.10E-03 -4.95E+00

/Natural gas/No. 6 Residual oil/Wood: Bark/ - - 79.04 - 16.02 

 

YES Biomass 2 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

Particulate Matter (PM) filterable 1 7/19/2009 4.26E-04 -7.76E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 63.71 18.74 

 

YES Biomass 2 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

Particulate Matter (PM) filterable 2 7/19/2009 8.72E-04 -7.05E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 63.71 18.74 

 

YES Biomass 2 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

Particulate Matter (PM) filterable 3 7/20/2009 4.42E-04 -7.72E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 63.71 18.74 

 

YES Biomass 2 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

Particulate Matter (PM) filterable Sample #1 3/22/2006 6.29E-03 -5.07E+00

/Hog Fuel/Industrial Sludge/Natural gas/ - - - 72.52 23.40 

 

YES Biomass 2 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

Particulate Matter (PM) filterable Sample #2 3/22/2006 8.21E-03 -4.80E+00

/Hog Fuel/Industrial Sludge/Natural gas/ - - - 72.52 23.40 

 

YES Biomass 2 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

Particulate Matter (PM) filterable Sample #3 3/22/2006 6.81E-03 -4.99E+00

/Hog Fuel/Industrial Sludge/Natural gas/ - - - 72.52 23.40 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #1 4/23/2008 6.00E-04 -7.42E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #1 4/22/2008 2.00E-03 -6.21E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #1 8/8/2008 7.00E-03 -4.96E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 90.50 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #2 4/22/2008 1.00E-03 -6.91E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #2 4/23/2008 8.00E-04 -7.13E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #2 8/8/2008 9.00E-03 -4.71E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 90.50 - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #3 8/8/2008 1.30E-02 -4.34E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 90.50 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #3 4/23/2008 4.00E-04 -7.82E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

 

YES Biomass 3 MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #3 4/22/2008 2.00E-03 -6.21E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #1 8/8/2008 7.00E-03 -4.96E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 90.50 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #1 4/22/2008 2.00E-03 -6.21E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #1 4/23/2008 6.00E-04 -7.42E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #2 4/22/2008 1.00E-03 -6.91E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #2 8/8/2008 9.00E-03 -4.71E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 90.50 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #2 4/23/2008 8.00E-04 -7.13E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #3 4/22/2008 2.00E-03 -6.21E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #3 8/8/2008 1.30E-02 -4.34E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 90.50 - 

 

YES Biomass 4 MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #3 4/23/2008 4.00E-04 -7.82E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #1 8/11/2009 ND 1.50E-03 -6.50E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #1 11/10/2004 7.00E-04 -7.26E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #1 9/18/1996 2.00E-03 -6.21E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #2 9/18/1996 2.00E-03 -6.21E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #2 8/11/2009 1.80E-03 -6.32E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #2 11/10/2004 7.00E-04 -7.26E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #3 8/12/2009 ND 6.00E-04 -7.42E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #3 11/10/2004 5.00E-04 -7.60E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 5 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #3 9/18/1996 2.00E-03 -6.21E+00 /Hog Fuel/ - - - 100.00 - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 6 ORFlakeboardEugene Boiler-2

Particulate Matter (PM) filterable Sample #1 8/26/2009 1.10E-03 -6.81E+00

Natural gas/Wood: Unadulterated Lumber

YES Biomass 6 ORFlakeboardEugene Boiler-2

Particulate Matter (PM) filterable Sample #2 8/27/2009 8.90E-04 -7.02E+00

Natural gas/Wood: Unadulterated Lumber

YES Biomass 6 ORFlakeboardEugene Boiler-2

Particulate Matter (PM) filterable Sample #3 8/27/2009 2.80E-04 -8.18E+00

Natural gas/Wood: Unadulterated Lumber

YES Biomass 7 ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable 1 9/9/2009 4.80E-03 -5.34E+00 Hog Fuel

YES Biomass 7 ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable 2 9/9/2009 3.30E-03 -5.71E+00 Hog Fuel

YES Biomass 7 ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable 3 9/10/2009 3.55E-02 -3.34E+00 Hog Fuel

YES Biomass 7 ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable Sample #1 8/8/2006 1.10E-03 -6.81E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 7 ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable Sample #2 8/8/2006 7.00E-04 -7.26E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 7 ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable Sample #3 8/8/2006 6.00E-04 -7.42E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 8 GAGPMadisonPly

800 Wood Waste Boiler

Particulate Matter (PM) 

filterable 1 8/11/2009 2.32E-03 -6.07E+00

Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins) - - 100.00 - - 

 

YES Biomass 8 GAGPMadisonPly

800 Wood Waste Boiler

Particulate Matter (PM) filterable 2 8/12/2009 2.26E-05 -1.07E+01

Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins) - - 100.00 - - 

 

YES Biomass 8 GAGPMadisonPly

800 Wood Waste Boiler

Particulate Matter (PM) filterable 3 8/12/2009 1.17E-03 -6.75E+00

Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins) - - 100.00 - - 

 

YES Biomass 8 GAGPMadisonPly

800 Wood Waste Boiler

Particulate Matter (PM) filterable Sample #1 6/19/2003 4.00E-03 -5.52E+00

/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/ - - 82.02 17.98 - 

 

YES Biomass 8 GAGPMadisonPly

800 Wood Waste Boiler

Particulate Matter (PM) filterable Sample #2 6/19/2003 2.00E-03 -6.21E+00

/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/ - - 82.02 17.98 - 

 

YES Biomass 8 GAGPMadisonPly

800 Wood Waste Boiler

Particulate Matter (PM) filterable Sample #3 6/19/2003 2.00E-03 -6.21E+00

/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/ - - 82.02 17.98 - 

 

YES Biomass 9 GAGPMonticelloPlywood

EU700 - Wood Waste Boiler

Particulate Matter (PM) filterable Sample #1 2/21/2008 2.00E-03 -6.21E+00

/MDF Scraps/Plywood Sander Dust/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 77.40 22.60 - 

 

YES Biomass 9 GAGPMonticelloPlywood

EU700 - Wood Waste Boiler

Particulate Matter (PM) filterable Sample #1 2/7/2007 5.00E-03 -5.30E+00

/MDF Scraps/Plywood Sander Dust/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 81.00 19.00 - 

 

YES Biomass 9 GAGPMonticelloPlywood

EU700 - Wood Waste Boiler

Particulate Matter (PM) filterable Sample #2 2/21/2008 1.00E-03 -6.91E+00

/MDF Scraps/Plywood Sander Dust/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 77.40 22.60 - 

 

YES Biomass 9 GAGPMonticelloPlywood

EU700 - Wood Waste Boiler

Particulate Matter (PM) filterable Sample #2 2/7/2007 7.00E-03 -4.96E+00

/MDF Scraps/Plywood Sander Dust/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 81.00 19.00 - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 9 GAGPMonticelloPlywood

EU700 - Wood Waste Boiler

Particulate Matter (PM) filterable Sample #3 2/21/2008 1.00E-03 -6.91E+00

/MDF Scraps/Plywood Sander Dust/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 77.40 22.60 - 

 

YES Biomass 9 GAGPMonticelloPlywood

EU700 - Wood Waste Boiler

Particulate Matter (PM) filterable Sample #3 2/7/2007 5.00E-03 -5.30E+00

/MDF Scraps/Plywood Sander Dust/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 81.00 19.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #1 7/22/2009 3.19E-03 -5.75E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #1 8/7/1997 2.43E-02 -3.72E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #1 12/5/2002 1.30E-03 -6.65E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #2 7/23/2009 3.87E-03 -5.55E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #2 8/7/1997 1.28E-02 -4.36E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #2 12/5/2002 1.50E-03 -6.50E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #3 12/5/2002 1.30E-03 -6.65E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #3 8/7/1997 9.70E-03 -4.64E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 10 ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #3 7/23/2009 4.17E-03 -5.48E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 9/29/2004 2.70E-03 -5.91E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/4/2002 5.40E-03 -5.22E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 11/9/2000 3.50E-03 -5.65E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/10/1999 1.60E-02 -4.14E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/5/2001 1.10E-02 -4.51E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 11/21/1998 5.80E-03 -5.15E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 8/11/1997 1.94E-02 -3.94E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/4/2003 2.30E-03 -6.07E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 11/9/2000 1.70E-03 -6.38E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 8/11/1997 1.47E-02 -4.22E+00 /Hog Fuel/ - - - 100.00 - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 11/21/1998 5.80E-03 -5.15E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/5/2001 6.40E-03 -5.05E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/10/1999 1.00E-02 -4.61E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/4/2002 4.80E-03 -5.34E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/4/2003 1.50E-03 -6.50E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 9/29/2004 3.60E-03 -5.63E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 11/21/1998 4.20E-03 -5.47E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/5/2001 2.74E-02 -3.60E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/4/2003 1.40E-03 -6.57E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 11/9/2000 1.80E-03 -6.32E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/10/1999 1.50E-02 -4.20E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/4/2002 4.30E-03 -5.45E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 9/29/2004 4.90E-03 -5.32E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 11 ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 8/11/1997 8.60E-03 -4.76E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 12 MSGPNewAugusta

AA-015 Power Boiler

Particulate Matter (PM) filterable Sample #1 7/12/2006 2.80E-03 -5.88E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 12 MSGPNewAugusta

AA-015 Power Boiler

Particulate Matter (PM) filterable Sample #2 7/12/2006 1.00E-03 -6.91E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 12 MSGPNewAugusta

AA-015 Power Boiler

Particulate Matter (PM) filterable Sample #3 7/12/2006 1.60E-03 -6.44E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 13 WAKimberlyClarkEverett

No. 14 Cogeneration Boiler

Particulate Matter (PM) filterable Sample #1 5/29/2008 2.09E-03 -6.17E+00

/Hog Fuel/Industrial Sludge/Paper and Paper Residues/ - - - 98.20 1.43 

 

YES Biomass 13 WAKimberlyClarkEverett

No. 14 Cogeneration Boiler

Particulate Matter (PM) filterable Sample #1 8/19/2009 2.00E-03 -6.21E+00 Hog Fuel/Natural gas

YES Biomass 13 WAKimberlyClarkEverett

No. 14 Cogeneration Boiler

Particulate Matter (PM) filterable Sample #2 8/20/2009 2.10E-03 -6.17E+00 Hog Fuel/Natural gas

YES Biomass 13 WAKimberlyClarkEverett

No. 14 Cogeneration Boiler

Particulate Matter (PM) filterable Sample #2 5/10/2006 7.95E-03 -4.83E+00

/Hog Fuel/Industrial Sludge/Paper and Paper Residues/ - - - 98.20 1.43 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 13 WAKimberlyClarkEverett

No. 14 Cogeneration Boiler

Particulate Matter (PM) filterable Sample #3 8/20/2009 1.50E-03 -6.50E+00 Hog Fuel/Natural gas

YES Biomass 13 WAKimberlyClarkEverett

No. 14 Cogeneration Boiler

Particulate Matter (PM) filterable Sample #3 5/9/2006 9.63E-03 -4.64E+00

/Hog Fuel/Industrial Sludge/Paper and Paper Residues/ - - - 98.20 1.43 

 

YES Biomass 14 MNBoisePaper1212

EU 430 Boiler #2

Particulate Matter (PM) filterable Sample #1 6/7/2005 5.94E-04 -7.43E+00

/Industrial Sludge - Primary/Industrial Sludge - Secondary/Natural gas/Wood: Bark/ - - 87.55 - 12.45 

 

YES Biomass 14 MNBoisePaper1212

EU 430 Boiler #2

Particulate Matter (PM) filterable Sample #2 6/7/2005 1.75E-03 -6.35E+00

/Industrial Sludge - Primary/Industrial Sludge - Secondary/Natural gas/Wood: Bark/ - - 87.55 - 12.45 

 

YES Biomass 14 MNBoisePaper1212

EU 430 Boiler #2

Particulate Matter (PM) filterable Sample #3 6/7/2005 3.30E-03 -5.71E+00

/Industrial Sludge - Primary/Industrial Sludge - Secondary/Natural gas/Wood: Bark/ - - 87.55 - 12.45 

 

YES Biomass 15 IDRileyCreekLumber HFB1

Particulate Matter (PM) filterable Sample #1 4/24/2003 3.04E-03 -5.80E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

 

YES Biomass 15 IDRileyCreekLumber HFB1

Particulate Matter (PM) filterable Sample #2 4/24/2003 1.85E-03 -6.29E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

 

YES Biomass 15 IDRileyCreekLumber HFB1

Particulate Matter (PM) filterable Sample #3 4/24/2003 1.45E-03 -6.53E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 6/2/2006 1.90E-03 -6.27E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 1/5/2007 1.00E-02 -4.61E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 1/10/2006 1.90E-02 -3.96E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 8/22/2006 1.01E-02 -4.60E+00 /Wood: Unadulterated Timber/ - - 100.00 - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 3/24/2005 4.30E-03 -5.45E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 11/30/2007 1.60E-02 -4.14E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 3/26/2005 3.40E-03 -5.68E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 8/22/2006 1.93E-02 -3.95E+00 /Wood: Unadulterated Timber/ - - 100.00 - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 11/30/2007 1.10E-02 -4.51E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 6/2/2006 2.60E-03 -5.95E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 3/26/2005 6.80E-03 -4.99E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 3/24/2005 3.40E-03 -5.68E+00 /Bagasse/ 100.00 - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 1/10/2006 2.00E-02 -3.91E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 1/5/2007 8.00E-03 -4.83E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 6/2/2006 2.20E-03 -6.12E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 3/24/2005 4.10E-03 -5.50E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 11/30/2007 1.70E-02 -4.07E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 1/10/2006 2.40E-02 -3.73E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 8/22/2006 1.67E-02 -4.09E+00 /Wood: Unadulterated Timber/ - - 100.00 - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 1/5/2007 1.10E-02 -4.51E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 16 FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 3/26/2005 7.80E-03 -4.85E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 17 IDPotlatchLewiston

4 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/16/2006 1.60E-03 -6.44E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.74 - 

 

YES Biomass 17 IDPotlatchLewiston

4 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/16/2006 2.90E-03 -5.84E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.74 - 

 

YES Biomass 17 IDPotlatchLewiston

4 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/16/2006 2.50E-03 -5.99E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.74 - 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #1 1/4/2007 2.00E-03 -6.21E+00

/Industrial Sludge/Natural gas/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 90.75 3.32 3.71 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #1 1/26/2005 1.20E-02 -4.42E+00

/Industrial Sludge/Natural gas/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 78.39 11.75 4.09 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #1 7/14/2009 2.50E-03 -5.99E+00

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #2 1/4/2007 3.00E-03 -5.81E+00

/Industrial Sludge/Natural gas/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 90.75 3.32 3.71 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #2 1/26/2005 1.00E-02 -4.61E+00

/Industrial Sludge/Natural gas/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 78.39 11.75 4.09 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #2 7/14/2009 2.70E-03 -5.91E+00

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #3 7/14/2009 2.00E-03 -6.21E+00

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #3 1/4/2007 2.00E-03 -6.21E+00

/Industrial Sludge/Natural gas/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 90.75 3.32 3.71 

 

YES Biomass 18 SCMarlboroPaper

Hogged Fuel Boiler

Particulate Matter (PM) filterable Sample #3 1/26/2005 3.00E-03 -5.81E+00

/Industrial Sludge/Natural gas/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 78.39 11.75 4.09 

 

YES Biomass 19 IDPotlatch PB-1 CE

Particulate Matter (PM) filterable Sample #1 4/30/2008 8.90E-03 -4.72E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 19 IDPotlatch PB-1 CE

Particulate Matter (PM) filterable Sample #1 7/28/2009 2.80E-03 -5.88E+00 Hog Fuel

YES Biomass 19 IDPotlatch PB-1 CE

Particulate Matter (PM) filterable Sample #2 7/28/2009 2.10E-03 -6.17E+00 Hog Fuel

YES Biomass 19 IDPotlatch PB-1 CE

Particulate Matter (PM) filterable Sample #2 4/30/2008 5.70E-03 -5.17E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 19 IDPotlatch PB-1 CE

Particulate Matter (PM) filterable Sample #3 7/29/2009 2.30E-03 -6.07E+00 Hog Fuel

YES Biomass 19 IDPotlatch PB-1 CE

Particulate Matter (PM) filterable Sample #3 4/30/2008 3.00E-03 -5.81E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 3/19/2008 1.18E-02 -4.44E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 78.65 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/13/1997 1.40E-02 -4.27E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/16/1995 5.80E-03 -5.15E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 3/25/2004 7.00E-03 -4.96E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 76.48 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 3/15/2006 5.30E-03 -5.24E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 79.64 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power 

Boiler

Particulate Matter (PM) filterable Sample #1 8/19/1993 7.10E-02 -2.65E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 6/5/2003 1.17E-02 -4.45E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 6/19/2001 1.65E-02 -4.10E+00 /No. 6 Residual oil/Wood: Bark/ - - 80.39 - 19.61 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #1 6/16/1999 1.40E-03 -6.57E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 3/15/2006 3.40E-03 -5.68E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 79.64 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 3/19/2008 1.17E-02 -4.45E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 78.65 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/19/1993 3.36E-02 -3.39E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/16/1995 4.20E-03 -5.47E+00 /Wood: Bark/ - - 100.00 - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 6/5/2003 6.50E-03 -5.04E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/13/1997 9.00E-03 -4.71E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 6/19/2001 7.80E-03 -4.85E+00 /No. 6 Residual oil/Wood: Bark/ - - 80.39 - 19.61 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 6/16/1999 3.90E-03 -5.55E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #2 3/25/2004 7.00E-03 -4.96E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 76.48 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/13/1997 2.30E-02 -3.77E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 6/19/2001 6.90E-03 -4.98E+00 /No. 6 Residual oil/Wood: Bark/ - - 80.39 - 19.61 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/16/1995 3.20E-03 -5.74E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 3/15/2006 4.00E-03 -5.52E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 79.64 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/19/1993 2.89E-02 -3.54E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 3/25/2004 1.10E-02 -4.51E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 76.48 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 6/16/1999 2.60E-03 -5.95E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 3/19/2008 3.90E-03 -5.55E+00

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 78.65 - - 

 

YES Biomass 20 SCInternationalPaperEastover

No. 2 Power Boiler

Particulate Matter (PM) filterable Sample #3 6/5/2003 5.00E-03 -5.30E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 21 FLSmurfit-Stone 5PB

Particulate Matter (PM) filterable Sample #1 7/10/2007 4.00E-03 -5.52E+00 /Biomass/No. 6 Residual oil/ - - - 51.85 48.15 

 

YES Biomass 21 FLSmurfit-Stone 5PB

Particulate Matter (PM) filterable Sample #2 7/10/2007 1.00E-03 -6.91E+00 /Biomass/No. 6 Residual oil/ - - - 51.85 48.15 

 

YES Biomass 21 FLSmurfit-Stone 5PB

Particulate Matter (PM) filterable Sample #3 7/10/2007 3.00E-03 -5.81E+00 /Biomass/No. 6 Residual oil/ - - - 51.85 48.15 

 

YES Biomass 22 MEBoralexStratton Boiler #1

Particulate Matter (PM) filterable Sample #1 10/21/2009 1.00E-03 -6.91E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 22 MEBoralexStratton Boiler #1

Particulate Matter (PM) filterable Sample #2 10/21/2009 3.00E-03 -5.81E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 22 MEBoralexStratton Boiler #1

Particulate Matter (PM) filterable Sample #3 10/21/2009 4.00E-03 -5.52E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 23 LAGPPortHudson

EQT0109 - No. 6 CFB Boiler

Particulate Matter (PM) filterable Sample #1 8/14/2007 3.00E-03 -5.81E+00

/Coke Oven Gas/Industrial Sludge/Wood: Bark/Wood: Unadulterated Lumber/ - - 13.24 0.69 3.06 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 23 LAGPPortHudson

EQT0109 - No. 6 CFB Boiler

Particulate Matter (PM) filterable Sample #3 8/14/2007 3.00E-03 -5.81E+00

/Coke Oven Gas/Industrial Sludge/Wood: Bark/Wood: Unadulterated Lumber/ - - 13.24 0.69 3.06 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #1 12/12/2007 6.00E-03 -5.12E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #1 7/11/2008 4.00E-03 -5.52E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #1 7/11/2008 4.00E-03 -5.52E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #1 12/12/2007 1.10E-02 -4.51E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #2 7/11/2008 2.00E-03 -6.21E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #2 12/12/2007 7.00E-03 -4.96E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #2 7/11/2008 4.00E-03 -5.52E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #2 12/12/2007 4.00E-03 -5.52E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #3 12/12/2007 1.40E-02 -4.27E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #3 7/11/2008 3.00E-03 -5.81E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 

Power Boiler

Particulate Matter (PM) filterable Sample #3 7/11/2008 3.00E-03 -5.81E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 24 ALGPBrewtonMill

BR-PSG0-S026 No. 3 Power Boiler

Particulate Matter (PM) filterable Sample #3 12/12/2007 6.00E-03 -5.12E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Coal 1 IAArchersDanielsMidlandDesM

Asea Boiler #1

Particulate Matter (PM) filterable Sample #1 8/26/2009 2.00E-04 -8.52E+00 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 1 IAArchersDanielsMidlandDesM

Asea Boiler #1

Particulate Matter (PM) filterable Sample #1 6/3/2008 7.06E-04 -7.26E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 1 IAArchersDanielsMidlandDesM

Asea Boiler #1

Particulate Matter (PM) filterable Sample #2 8/26/2009 2.00E-04 -8.52E+00 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 1 IAArchersDanielsMidlandDesM

Asea Boiler #1

Particulate Matter (PM) filterable Sample #2 6/3/2008 5.34E-04 -7.53E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 1 IAArchersDanielsMidlandDesM

Asea Boiler #1

Particulate Matter (PM) filterable Sample #3 8/27/2009 2.00E-04 -8.52E+00 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 1 IAArchersDanielsMidlandDesM

Asea Boiler #1

Particulate Matter (PM) filterable Sample #3 6/3/2008 5.37E-04 -7.53E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #1 5/9/2007 9.90E-03 -4.62E+00 /Coal: Bituminous/Industrial Sludge/ - 96.87 - - 3.13 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #1 5/10/2007 6.70E-03 -5.01E+00

/Coal: Bituminous/Plant-based Agricultural Residue/ - 88.40 - 11.60 - 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #1 8/14/2007 8.00E-03 -4.83E+00

/Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue/ - 84.07 - 13.43 2.50 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #1 8/15/2007 1.22E-02 -4.41E+00 /Coal: Bituminous/Industrial Sludge/ - 97.50 - - 2.50 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #1 10/15/2009 3.40E-04 -7.99E+00

Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue - 61.99 - 9.40 28.61 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #1 5/8/2007 8.10E-03 -4.82E+00

/Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue/ - 85.85 - 11.23 2.92 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #2 5/8/2007 7.70E-03 -4.87E+00

/Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue/ - 85.85 - 11.23 2.92 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #2 10/16/2009 7.03E-04 -7.26E+00

Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue - 61.99 - 9.40 28.61 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #2 5/9/2007 1.24E-02 -4.39E+00 /Coal: Bituminous/Industrial Sludge/ - 96.87 - - 3.13 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #2 8/14/2007 1.01E-02 -4.60E+00

/Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue/ - 84.07 - 13.43 2.50 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #2 5/10/2007 5.50E-03 -5.20E+00

/Coal: Bituminous/Plant-based Agricultural Residue/ - 88.40 - 11.60 - 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #2 8/15/2007 9.90E-03 -4.62E+00 /Coal: Bituminous/Industrial Sludge/ - 97.50 - - 2.50 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #3 5/10/2007 9.90E-03 -4.62E+00

/Coal: Bituminous/Plant-based Agricultural Residue/ - 88.40 - 11.60 - 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #3 8/15/2007 1.23E-02 -4.40E+00 /Coal: Bituminous/Industrial Sludge/ - 97.50 - - 2.50 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #3 8/14/2007 6.70E-03 -5.01E+00

/Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue/ - 84.07 - 13.43 2.50 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #3 5/9/2007 5.90E-03 -5.13E+00 /Coal: Bituminous/Industrial Sludge/ - 96.87 - - 3.13 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #3 10/16/2009 4.41E-04 -7.73E+00

Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue - 61.99 - 9.40 28.61 

 

YES Coal 2 IAMonsantoMuscatine

Boiler #8 (EP195)

Particulate Matter (PM) filterable Sample #3 5/8/2007 6.50E-03 -5.04E+00

/Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue/ - 85.85 - 11.23 2.92 

 

YES Coal 3 IAUofNorthernIowa Boiler #3

Particulate Matter (PM) filterable 4 10/6/2009 7.97E-04 -7.13E+00 Coal: Bituminous - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 3 IAUofNorthernIowa Boiler #3

Particulate Matter (PM) filterable 5 10/6/2009 6.03E-04 -7.41E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 3 IAUofNorthernIowa Boiler #3

Particulate Matter (PM) filterable 6 10/7/2009 3.73E-04 -7.89E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable M027-1 9/17/2009 1.27E-03 -6.67E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable M027-2 9/17/2009 4.51E-04 -7.70E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable M027-3 9/18/2009 7.12E-04 -7.25E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable Sample #1 12/6/2007 9.00E-04 -7.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 4 VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable Sample #2 12/6/2007 5.00E-04 -7.60E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 4 VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable Sample #3 12/6/2007 4.00E-04 -7.82E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 5 IAIAStateUnivPowerPlant B2

Particulate Matter (PM) filterable Sample #1 3/27/2008 5.05E-04 -7.59E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 5 IAIAStateUnivPowerPlant B2

Particulate Matter (PM) filterable Sample #2 3/27/2008 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 5 IAIAStateUnivPowerPlant B2

Particulate Matter (PM) filterable Sample #3 3/27/2008 3.18E-04 -8.05E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 6 WIGreenBayPackagingMillDivis

Boiler B26- Coal Fired Boiler

Particulate Matter (PM) filterable Sample #1 5/16/2006 1.07E-03 -6.84E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 6 WIGreenBayPackagingMillDivis

Boiler B26- Coal Fired Boiler

Particulate Matter (PM) filterable Sample #2 5/16/2006 4.00E-05 -1.01E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 6 WIGreenBayPackagingMillDivis

Boiler B26- Coal Fired Boiler

Particulate Matter (PM) filterable Sample #3 5/16/2006 8.10E-04 -7.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable 1 8/5/2009 7.14E-04 -7.24E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 7 TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable 2 11/6/2009 7.81E-04 -7.15E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 7 TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable 3 8/6/2009 DLL 6.40E-04 -7.35E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 7 TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable Sample #1 7/17/2007 2.10E-02 -3.86E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable Sample #2 7/17/2007 1.78E-02 -4.03E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable Sample #3 7/17/2007 1.33E-02 -4.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 8 PAPHGlatfelter PB5

Particulate Matter (PM) filterable Sample #1 7/13/2006 4.56E-03 -5.39E+00

/Coal: Bituminous/Industrial Sludge/Wood: Unadulterated Timber/ - 65.14 23.93 - 10.93 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 8 PAPHGlatfelter PB5

Particulate Matter (PM) filterable Sample #1 8/18/2009 6.96E-04 -7.27E+00

Coal: Bituminous/Industrial Sludge/Wood: Bark

YES Coal 8 PAPHGlatfelter PB5

Particulate Matter (PM) filterable Sample #2 7/13/2006 5.74E-03 -5.16E+00

/Coal: Bituminous/Industrial Sludge/Wood: Unadulterated Timber/ - 65.14 23.93 - 10.93 

 

YES Coal 8 PAPHGlatfelter PB5

Particulate Matter (PM) filterable Sample #2 8/18/2009 1.27E-03 -6.67E+00

Coal: Bituminous/Industrial Sludge/Wood: Bark

YES Coal 8 PAPHGlatfelter PB5

Particulate Matter (PM) filterable Sample #3 8/19/2009 6.11E-04 -7.40E+00

Coal: Bituminous/Industrial Sludge/Wood: Bark

YES Coal 8 PAPHGlatfelter PB5

Particulate Matter (PM) filterable Sample #3 7/13/2006 5.34E-03 -5.23E+00

/Coal: Bituminous/Industrial Sludge/Wood: Unadulterated Timber/ - 65.14 23.93 - 10.93 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 7/24/2008 4.80E-03 -5.34E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 8/8/2000 6.40E-02 -2.75E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 11/9/2004 1.30E-03 -6.65E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 11/10/2004 8.00E-04 -7.13E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 8/20/1996 1.69E-02 -4.08E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 11/10/2004 1.40E-03 -6.57E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 7/24/2008 5.90E-03 -5.13E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 11/9/2004 2.30E-03 -6.07E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 6/29/2004 1.86E-02 -3.98E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 8/20/1996 1.15E-02 -4.47E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 8/8/2000 2.27E-02 -3.79E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 11/10/2004 1.80E-03 -6.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 7/24/2008 8.50E-03 -4.77E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 8/8/2000 1.33E-02 -4.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 8/20/1996 5.21E-02 -2.95E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 6/29/2004 3.00E-03 -5.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 9 TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 11/11/2004 4.00E-04 -7.82E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 10 IAIAStateUnivPowerPlant B1

Particulate Matter (PM) filterable Sample #1 3/26/2008 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 10 IAIAStateUnivPowerPlant B1

Particulate Matter (PM) filterable Sample #2 3/26/2008 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 10 IAIAStateUnivPowerPlant B1

Particulate Matter (PM) filterable Sample #3 3/26/2008 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 11 OHSmartPapersHoldingsLLC B010

Particulate Matter (PM) filterable Sample #1 8/11/2005 1.10E-03 -6.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 11 OHSmartPapersHoldingsLLC B010

Particulate Matter (PM) filterable Sample #2 8/11/2005 5.00E-04 -7.60E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 11 OHSmartPapersHoldingsLLC B010

Particulate Matter (PM) filterable Sample #3 8/11/2005 1.40E-03 -6.57E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 9/25/1997 1.23E-02 -4.40E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 5/17/2005 3.10E-03 -5.78E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 8/28/2001 1.31E-02 -4.34E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 3/10/2005 2.40E-03 -6.03E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 3/9/2005 1.20E-03 -6.73E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 7/12/1993 1.82E-02 -4.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 3/9/2005 1.60E-03 -6.44E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 9/25/1997 5.90E-03 -5.13E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 8/28/2001 4.00E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 5/17/2005 5.80E-03 -5.15E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 7/12/1993 9.90E-03 -4.62E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 3/10/2005 9.30E-04 -6.98E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 5/17/2005 2.70E-03 -5.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 7/12/1993 1.52E-02 -4.19E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 3/9/2005 8.00E-04 -7.13E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 9/25/1997 4.02E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 3/10/2005 2.20E-03 -6.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 8/28/2001 5.00E-03 -5.30E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable 1 9/22/2009 1.28E-03 -6.66E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable 1 9/22/2009 1.28E-03 -6.66E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable 2 9/22/2009 1.54E-03 -6.48E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable 2 8/6/2009 1.19E-03 -6.74E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable 3 8/5/2009 1.68E-03 -6.39E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable 3 9/23/2009 1.25E-03 -6.69E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable Sample #1 9/12/2007 4.60E-03 -5.38E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable Sample #2 9/12/2007 3.00E-03 -5.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 13 WINewPageBiron B24

Particulate Matter (PM) filterable Sample #3 9/12/2007 3.60E-03 -5.63E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 14 IDTASCONampa Riley Boiler

Particulate Matter (PM) filterable Sample #1 1/12/2004 1.56E-03 -6.46E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 14 IDTASCONampa Riley Boiler

Particulate Matter (PM) filterable Sample #2 1/12/2004 1.43E-03 -6.55E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 14 IDTASCONampa Riley Boiler

Particulate Matter (PM) filterable Sample #3 1/12/2004 1.35E-03 -6.61E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 15 MENewPage-Rumford Cogen#6

Particulate Matter (PM) filterable 1 12/8/2009 1.27E-03 -6.67E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 15 MENewPage-Rumford Cogen#6

Particulate Matter (PM) filterable 2 12/8/2009 1.44E-03 -6.54E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 15 MENewPage-Rumford Cogen#6

Particulate Matter (PM) filterable 3 12/9/2009 1.72E-03 -6.37E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 15 MENewPage-Rumford Cogen#6

Particulate Matter (PM) filterable Sample #1 9/6/2007 6.00E-03 -5.12E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.47 - 33.37 1.73 

 

YES Coal 15 MENewPage-Rumford Cogen#6

Particulate Matter (PM) filterable Sample #2 9/6/2007 2.00E-03 -6.21E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.47 - 33.37 1.73 

 

YES Coal 15 MENewPage-Rumford Cogen#6

Particulate Matter (PM) filterable Sample #3 9/6/2007 5.00E-03 -5.30E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.47 - 33.37 1.73 

 

YES Coal 16 MENewPage-Rumford Cogen#7

Particulate Matter (PM) filterable 1 12/8/2009 1.27E-03 -6.67E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 16 MENewPage-Rumford Cogen#7

Particulate Matter (PM) filterable 2 12/8/2009 1.44E-03 -6.54E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 16 MENewPage-Rumford Cogen#7

Particulate Matter (PM) filterable 3 12/9/2009 1.72E-03 -6.37E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 16 MENewPage-Rumford Cogen#7

Particulate Matter (PM) filterable Sample #1 9/6/2007 6.00E-03 -5.12E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.47 - 33.37 1.73 

 

YES Coal 16 MENewPage-Rumford Cogen#7

Particulate Matter (PM) filterable Sample #2 9/6/2007 2.00E-03 -6.21E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.47 - 33.37 1.73 

 

YES Coal 16 MENewPage-Rumford Cogen#7

Particulate Matter (PM) filterable Sample #3 9/6/2007 5.00E-03 -5.30E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.47 - 33.37 1.73 

 

YES Coal 17 INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #1 4/7/2005 1.50E-03 -6.50E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #1 6/28/2006 1.60E-03 -6.44E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate 

Matter (PM) filterable Sample #2 4/7/2005 9.00E-04 -7.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #2 6/28/2006 9.00E-04 -7.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #3 6/28/2006 3.00E-03 -5.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #3 4/7/2005 2.20E-03 -6.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #1 4/7/2005 1.50E-03 -6.50E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #1 6/28/2006 1.60E-03 -6.44E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #2 4/7/2005 9.00E-04 -7.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #2 6/28/2006 9.00E-04 -7.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 18 INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #3 4/7/2005 2.20E-03 -6.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #3 6/28/2006 3.00E-03 -5.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #1 11/3/2005 5.40E-02 -2.92E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #1 11/2/2005 1.90E-03 -6.27E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #1 10/31/2005 3.70E-03 -5.60E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #2 10/31/2005 2.40E-03 -6.03E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #2 11/3/2005 2.71E-02 -3.61E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #2 11/2/2005 2.80E-03 -5.88E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #3 11/3/2005 1.76E-02 -4.04E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #3 11/2/2005 5.00E-04 -7.60E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #3 10/31/2005 5.00E-03 -5.30E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 IAADMCornProcessingCR EU-502B

Particulate Matter (PM) filterable Sample #1 11/28/1994 1.80E-03 -6.32E+00

/Coal: Bituminous/Coal: Subbituminous/ - 100.00 - - - 

 

YES Coal 20 IAADMCornProcessingCR EU-502B

Particulate Matter (PM) filterable Sample #2 11/28/1994 3.80E-03 -5.57E+00

/Coal: Bituminous/Coal: Subbituminous/ - 100.00 - - - 

 

YES Coal 20 IAADMCornProcessingCR EU-502B

Particulate Matter (PM) filterable Sample #3 11/28/1994 1.00E-03 -6.91E+00

/Coal: Bituminous/Coal: Subbituminous/ - 100.00 - - - 

 

YES Coal 21 WIWausau

# 5 Power Boiler (B24)

Particulate Matter (PM) filterable Sample #1 7/24/2007 ND 1.34E-03 -6.62E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 21 WIWausau

# 5 Power Boiler (B24)

Particulate Matter (PM) filterable Sample #2 7/24/2007 3.56E-03 -5.64E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 21 WIWausau

# 5 Power Boiler (B24)

Particulate Matter (PM) filterable Sample #3 7/24/2007 2.02E-03 -6.20E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 22 AKDoyonUtilities_AK 4

Particulate Matter (PM) filterable Sample #1 8/17/2005 2.00E-03 -6.21E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 22 AKDoyonUtilities_AK 4

Particulate Matter (PM) filterable Sample #2 8/17/2005 2.30E-03 -6.07E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 22 AKDoyonUtilities_AK 4

Particulate Matter (PM) filterable Sample #3 8/17/2005 2.70E-03 -5.91E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 23 INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable M5-1 7/21/2009 2.79E-03 -5.88E+00 Coal: Bituminous - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 23 INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable M5-2 7/21/2009 2.82E-03 -5.87E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 23 INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable M5-3 7/22/2009 2.77E-03 -5.89E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 23 INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable Sample #1 11/29/2006 5.00E-03 -5.30E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable Sample #2 11/29/2006 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable Sample #3 11/29/2006 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 24 VAUniversityofVirginia 7103-1-02R

Particulate Matter (PM) filterable Sample #1 1/16/2007 4.00E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 24 VAUniversityofVirginia 7103-1-02R

Particulate Matter (PM) filterable Sample #2 1/16/2007 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 24 VAUniversityofVirginia 7103-1-02R

Particulate Matter (PM) filterable Sample #3 1/16/2007 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable 1 8/26/2009 4.65E-03 -5.37E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable 2 8/27/2009 1.73E-03 -6.36E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable 3 8/27/2009 1.42E-03 -6.56E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 9/19/2002 3.00E-03 -5.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 9/19/2006 9.90E-03 -4.62E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 12/29/1993 2.16E-02 -3.84E+00 /Coal: Bituminous/Process gas/

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 11/8/1994 9.10E-03 -4.70E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 11/8/1994 6.60E-03 -5.02E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 9/19/2006 1.33E-02 -4.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 9/19/2002 ND 2.70E-03 -5.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 12/29/1993 1.41E-02 -4.26E+00 /Coal: Bituminous/Process gas/

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 11/8/1994 7.10E-03 -4.95E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 9/19/2006 9.30E-03 -4.68E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 9/19/2002 3.20E-03 -5.74E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 12/29/1993 1.56E-02 -4.16E+00 /Coal: Bituminous/Process gas/

YES Coal 26 WAWeyerhaeuserLongview

No. 11 Hog Fuel Boiler

Particulate Matter (PM) filterable Sample #1 10/7/2008 2.00E-03 -6.21E+00

/Coal: Bituminous/Hog Fuel/Industrial Sludge/ - 34.08 - 55.26 10.66 

 

YES Coal 26 WAWeyerhaeuserLongview

No. 11 Hog Fuel Boiler

Particulate Matter (PM) filterable Sample #2 10/7/2008 3.00E-03 -5.81E+00

/Coal: Bituminous/Hog Fuel/Industrial Sludge/ - 34.08 - 55.26 10.66 

 

YES Coal 26 WAWeyerhaeuserLongview

No. 11 Hog Fuel Boiler

Particulate Matter (PM) filterable Sample #3 10/7/2008 3.00E-03 -5.81E+00

/Coal: Bituminous/Hog Fuel/Industrial Sludge/ - 34.08 - 55.26 10.66 

 

YES Coal 27 ILRockIslandArsenal

NBN 12602 (Boiler #1)

Particulate Matter (PM) filterable Sample #1 3/13/2007 4.26E-03 -5.46E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27 ILRockIslandArsenal

NBN 12602 (Boiler #1)

Particulate Matter (PM) filterable Sample #2 3/13/2007 2.43E-03 -6.02E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27 ILRockIslandArsenal

NBN 12602 (Boiler #1)

Particulate Matter (PM) filterable Sample #3 3/13/2007 1.39E-03 -6.58E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 OHUofCincinnati B108

Particulate Matter (PM) filterable Sample #1 4/26/2006 2.90E-03 -5.84E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 OHUofCincinnati B108

Particulate Matter (PM) filterable Sample #2 4/26/2006 3.03E-03 -5.80E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 OHUofCincinnati B108

Particulate Matter (PM) filterable Sample #3 4/27/2005 2.40E-03 -6.03E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/19/2004 1.37E-02 -4.29E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/9/2002 3.60E-02 -3.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/25/2006 3.30E-03 -5.71E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/24/2000 5.90E-02 -2.83E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/9/2002 4.40E-02 -3.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/24/2000 2.20E-02 -3.82E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/19/2004 5.10E-03 -5.28E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/25/2006 4.20E-03 -5.47E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/24/2000 4.40E-02 -3.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/9/2002 3.40E-02 -3.38E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/25/2006 1.20E-03 -6.73E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/19/2004 2.80E-03 -5.88E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 30 WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #1 2/23/2006 4.36E-03 -5.44E+00

/Coal: Bituminous/Paper and Paper Residues/ - 84.11 - - - 

 

YES Coal 30 WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #1 2/22/2006 4.89E-03 -5.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 30 WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #2 2/22/2006 1.58E-03 -6.45E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 30 WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #2 2/23/2006 5.79E-03 -5.15E+00

/Coal: Bituminous/Paper and Paper Residues/ - 84.11 - - - 

 

YES Coal 30 WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #3 2/22/2006 2.34E-03 -6.06E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 30 WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #3 2/23/2006 3.24E-03 -5.73E+00

/Coal: Bituminous/Paper and Paper Residues/ - 84.11 - - - 

 

YES Coal 31 WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #1 2/23/2006 4.36E-03 -5.44E+00

/Coal: Bituminous/Paper and Paper Residues/ - 84.11 - - - 

 

YES Coal 31 WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #1 2/22/2006 4.89E-03 -5.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 31 WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #2 2/22/2006 1.58E-03 -6.45E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 31 WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #2 2/23/2006 5.79E-03 -5.15E+00

/Coal: Bituminous/Paper and Paper Residues/ - 84.11 - - - 

 

YES Coal 31 WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #3 2/23/2006 3.24E-03 -5.73E+00

/Coal: Bituminous/Paper and Paper Residues/ - 84.11 - - - 

 

YES Coal 31 WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #3 2/22/2006 2.34E-03 -6.06E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 IDAmalgamatedSugarCoTwinF S-B1

Particulate Matter (PM) filterable Sample #1 9/26/2006 2.01E-03 -6.21E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 32 IDAmalgamatedSugarCoTwinF S-B1

Particulate Matter (PM) filterable Sample #2 9/26/2006 3.26E-03 -5.72E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 32 IDAmalgamatedSugarCoTwinF S-B1

Particulate Matter (PM) filterable Sample #3 9/26/2006 4.10E-03 -5.50E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPolyOne B1

Particulate Matter (PM) filterable 1 9/9/2009 4.59E-03 -5.38E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPolyOne B1

Particulate Matter (PM) filterable 2 9/9/2009 5.32E-03 -5.24E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPolyOne B1

Particulate Matter (PM) filterable 3 9/10/2009 1.26E-02 -4.37E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPolyOne B1

Particulate Matter (PM) filterable Sample #1 11/14/2006 3.20E-03 -5.74E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 34 FLSmurfit-Stone 7PB

Particulate Matter (PM) filterable Sample #1 7/11/2007 2.86E-03 -5.86E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 FLSmurfit-Stone 7PB

Particulate Matter (PM) filterable Sample #2 7/11/2007 1.50E-03 -6.50E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 FLSmurfit-Stone 7PB

Particulate Matter (PM) filterable Sample #3 7/11/2007 5.35E-03 -5.23E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 35 MESDWarren #21 Boiler

Particulate Matter (PM) filterable Sample #1 11/10/2006 4.00E-03 -5.52E+00

/Biomass/Coal: Bituminous/Industrial Sludge/ - 18.04 - 80.96 1.00 

 

YES Coal 35 MESDWarren #21 Boiler

Particulate Matter (PM) filterable Sample #2 11/10/2006 4.00E-03 -5.52E+00

/Biomass/Coal: Bituminous/Industrial Sludge/ - 18.04 - 80.96 1.00 

 

YES Coal 35 MESDWarren #21 Boiler

Particulate Matter (PM) filterable Sample #3 11/10/2006 2.00E-03 -6.21E+00

/Biomass/Coal: Bituminous/Industrial Sludge/ - 18.04 - 80.96 1.00 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 8/4/1994 3.30E-03 -5.71E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 12/6/2006 4.50E-03 -5.40E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 8/14/2006 4.21E-02 -3.17E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 9/29/1998 1.24E-02 -4.39E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 12/14/1994 9.10E-03 -4.70E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 9/17/2002 8.30E-03 -4.79E+00 /Coal: Bituminous/Process gas/

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 3/15/2005 5.00E-03 -5.30E+00 /Coal: Bituminous/Process gas/

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 7/25/2006 6.19E-02 -2.78E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 12/6/2006 2.70E-03 -5.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 8/4/1994 2.90E-03 -5.84E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 12/15/1994 2.80E-03 -5.88E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 9/29/1998 6.51E-03 -5.03E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 9/17/2002 7.00E-03 -4.96E+00 /Coal: Bituminous/Process gas/

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 3/15/2005 5.00E-03 -5.30E+00 /Coal: Bituminous/Process gas/

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) 

filterable Sample #2 7/25/2006 2.20E-02 -3.82E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 8/14/2006 4.59E-02 -3.08E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 12/6/2006 3.20E-03 -5.74E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 12/15/1994 6.70E-03 -5.01E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 8/14/2006 5.45E-02 -2.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 7/25/2006 4.15E-02 -3.18E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 3/15/2005 4.80E-03 -5.34E+00 /Coal: Bituminous/Process gas/

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 9/17/2002 4.90E-03 -5.32E+00 /Coal: Bituminous/Process gas/

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) 

filterable Sample #3 9/29/1998 9.68E-03 -4.64E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36 TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 8/4/1994 4.50E-03 -5.40E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable 1 8/4/2009 4.18E-03 -5.48E+00 Biomass/Coal: Bituminous - 51.03 - 48.97 - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable 2 8/5/2009 3.30E-03 -5.71E+00 Biomass/Coal: Bituminous - 51.03 - 48.97 - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable 3 8/5/2009 3.11E-03 -5.77E+00 Biomass/Coal: Bituminous - 51.03 - 48.97 - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #1 2/22/2006 4.10E-03 -5.50E+00 /Biomass/Coal: Bituminous/ - 23.18 - 76.82 - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #1 2/15/2006 5.40E-03 -5.22E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #2 2/21/2006 6.60E-03 -5.02E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #2 2/23/2006 3.20E-03 -5.74E+00 /Biomass/Coal: Bituminous/ - 23.18 - 76.82 - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #3 2/21/2006 7.00E-03 -4.96E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #3 2/23/2006 3.80E-03 -5.57E+00 /Biomass/Coal: Bituminous/ - 23.18 - 76.82 - 

 

YES Coal 38 ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable OTM28-1 8/4/2009 3.89E-03 -5.55E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 38 ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable OTM28-2 8/5/2009 3.06E-03 -5.79E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 38 ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable OTM28-3 8/5/2009 3.82E-03 -5.57E+00 Coal: Bituminous - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 38 ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable Sample #1 8/22/2007 2.10E-02 -3.86E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 38 ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable Sample #2 8/22/2007 2.30E-02 -3.77E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 38 ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable Sample #3 8/22/2007 1.90E-02 -3.96E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #1 10/12/2004 2.40E-02 -3.73E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #1 10/12/2004 4.00E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #2 10/12/2004 1.20E-02 -4.42E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #2 10/12/2004 3.00E-03 -5.81E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #3 10/12/2004 4.00E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #3 10/12/2004 1.00E-02 -4.61E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 40 OHSmartPapersHoldingsLLC B020

Particulate Matter (PM) filterable Sample #1 9/22/2005 6.50E-03 -5.04E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 40 OHSmartPapersHoldingsLLC B020

Particulate Matter (PM) filterable Sample #2 9/22/2005 5.00E-04 -7.60E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 40 OHSmartPapersHoldingsLLC B020

Particulate Matter (PM) filterable Sample #3 9/22/2005 4.20E-03 -5.47E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 41 AKDoyonUtilities_AK 7

Particulate Matter (PM) filterable Sample #1 8/16/2005 3.30E-03 -5.71E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 41 AKDoyonUtilities_AK 7

Particulate Matter (PM) filterable Sample #2 8/16/2005 4.20E-03 -5.47E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 41 AKDoyonUtilities_AK 7

Particulate Matter (PM) filterable Sample #3 8/16/2005 4.00E-03 -5.52E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 42 VAGPBigIsland2703

PWR04 - No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 5/1/2007 4.40E-03 -5.43E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 42 VAGPBigIsland2703

PWR04 - No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 5/1/2007 3.80E-03 -5.57E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 42 VAGPBigIsland2703

PWR04 - No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 5/1/2007 3.80E-03 -5.57E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 43 VAUniversityofVirginia 7103-1-05

Particulate Matter (PM) filterable Sample #1 4/4/2008 1.80E-03 -6.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 43 VAUniversityofVirginia 7103-1-05

Particulate Matter (PM) filterable Sample #2 4/4/2008 1.80E-03 -6.32E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 43 VAUniversityofVirginia 7103-1-05

Particulate Matter (PM) filterable Sample #3 4/4/2008 9.00E-03 -4.71E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 44 VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #1 4/14/2004 4.80E-02 -3.04E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 44 VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #1 10/14/2004 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 44 VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #2 4/14/2004 2.60E-02 -3.65E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 44 VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #2 10/14/2004 4.00E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 44 VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #3 10/14/2004 7.00E-03 -4.96E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 44 VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #3 4/14/2004 2.90E-02 -3.54E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Gas 1 1 IAADMClinton

EUCOG-5 #2 Gas Fired Boiler

Particulate Matter (PM) filterable Sample #1 3/5/2008 1.00E-04 -9.21E+00 /Natural gas/ - - - - - 

 

YES Gas 1 1 IAADMClinton

EUCOG-5 #2 Gas Fired Boiler

Particulate Matter (PM) filterable Sample #2 3/7/2008 2.00E-04 -8.52E+00 /Natural gas/ - - - - - 

 

YES Gas 1 1 IAADMClinton

EUCOG-5 #2 Gas Fired Boiler

Particulate Matter (PM) filterable Sample #3 3/10/2008 1.00E-04 -9.21E+00 /Natural gas/ - - - - - 

 

YES Gas 1 2 MSChevronPascagoula F-2103

Particulate Matter (PM) filterable Sample #1 3/27/2008 1.20E-04 -9.03E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 2 MSChevronPascagoula F-2103

Particulate Matter (PM) filterable Sample #2 3/27/2008 1.20E-04 -9.03E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 2 MSChevronPascagoula F-2103

Particulate Matter (PM) filterable Sample #3 3/27/2008 5.60E-04 -7.49E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 3 IACargillEddyville 84.000

Particulate Matter (PM) filterable Sample #1 11/25/1997 3.14E-04 -8.06E+00 /Natural gas/ - - - - - 

 

YES Gas 1 3 IACargillEddyville 84.000

Particulate Matter (PM) filterable Sample #2 11/25/1997 2.83E-04 -8.17E+00 /Natural gas/ - - - - - 

 

YES Gas 1 3 IACargillEddyville 84.000

Particulate Matter (PM) filterable Sample #3 11/25/1997 2.52E-04 -8.29E+00 /Natural gas/ - - - - - 

 

YES Gas 1 4 IACargillEddyville 86.000

Particulate Matter (PM) filterable Sample #1 11/25/1997 3.14E-04 -8.06E+00 /Natural gas/ - - - - - 

 

YES Gas 1 4 IACargillEddyville 86.000

Particulate Matter (PM) filterable Sample #2 11/25/1997 2.83E-04 -8.17E+00 /Natural gas/ - - - - - 

 

YES Gas 1 4 IACargillEddyville 86.000

Particulate Matter (PM) filterable Sample #3 11/25/1997 2.52E-04 -8.29E+00 /Natural gas/ - - - - - 

 

YES Gas 1 5 MABostonGeneratingMysticStaEU-17

Particulate Matter (PM) filterable Sample #1 8/14/2008 4.00E-04 -7.82E+00 /Natural gas/ - - - - - 

 

YES Gas 1 5 MABostonGeneratingMysticStaEU-17

Particulate Matter (PM) filterable Sample #2 8/14/2008 4.00E-04 -7.82E+00 /Natural gas/ - - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 5 MABostonGeneratingMysticStaEU-17

Particulate Matter (PM) filterable Sample #3 8/14/2008 1.00E-04 -9.21E+00 /Natural gas/ - - - - - 

 

YES Gas 1 6 MSDuPontDeLisle1342

AH-202 (BLR1342)

Particulate Matter (PM) filterable Sample #1 3/29/2007 3.76E-04 -7.89E+00 /Natural gas/ - - - - - 

 

YES Gas 1 6 MSDuPontDeLisle1342

AH-202 (BLR1342)

Particulate Matter (PM) filterable Sample #2 3/29/2007 2.27E-04 -8.39E+00 /Natural gas/ - - - - - 

 

YES Gas 1 6 MSDuPontDeLisle1342

AH-202 (BLR1342)

Particulate Matter (PM) filterable Sample #3 3/29/2007 3.45E-04 -7.97E+00 /Natural gas/ - - - - - 

 

YES Gas 1 7 IAKochNitrogen

ReformerAux Boiler

Particulate Matter (PM) filterable Sample #1 1/4/2007 6.17E-04 -7.39E+00 /Natural gas/Process gas/ - - - - - 

 

YES Gas 1 7 IAKochNitrogen

ReformerAux Boiler

Particulate Matter (PM) filterable Sample #2 1/4/2007 2.03E-04 -8.50E+00 /Natural gas/Process gas/ - - - - - 

 

YES Gas 1 7 IAKochNitrogen

ReformerAux Boiler

Particulate Matter (PM) filterable Sample #3 1/5/2007 2.55E-04 -8.27E+00 /Natural gas/Process gas/ - - - - - 

 

YES Gas 1 8 NCCampLejeuneMCB

C-AS-4151-16

Particulate Matter (PM) filterable Sample #1 9/30/2009 3.10E-04 -8.08E+00 Natural gas - - - - - 

 

YES Gas 1 8 NCCampLejeuneMCB

C-AS-4151-16

Particulate Matter (PM) filterable Sample #2 10/1/2009 4.40E-04 -7.73E+00 Natural gas - - - - - 

 

YES Gas 1 8 NCCampLejeuneMCB

C-AS-4151-16

Particulate Matter (PM) filterable Sample #3 10/1/2009 5.10E-04 -7.58E+00 Natural gas - - - - - 

 

YES Gas 1 9 IAGrainProcessing Boiler #10

Particulate Matter (PM) filterable Sample #1 7/24/2007 5.73E-04 -7.47E+00 /Natural gas/ - - - - - 

 

YES Gas 1 9 IAGrainProcessing Boiler #10

Particulate Matter (PM) filterable Sample #2 7/24/2007 5.73E-04 -7.47E+00 /Natural gas/ - - - - - 

 

YES Gas 1 9 IAGrainProcessing Boiler #10

Particulate Matter (PM) filterable Sample #3 7/24/2007 1.43E-04 -8.85E+00 /Natural gas/ - - - - - 

 

YES Gas 1 10 TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #1 6/11/2003 6.00E-04 -7.42E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 10 TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #2 6/11/2003 4.00E-04 -7.82E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 10 TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #3 6/11/2003 3.00E-04 -8.11E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 10 TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #3 12/11/2002 7.00E-04 -7.26E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 11 MSChevronPascagoula F-8510

Particulate Matter (PM) filterable Sample #1 11/6/2007 4.44E-04 -7.72E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 11 MSChevronPascagoula F-8510

Particulate Matter (PM) filterable Sample #2 11/6/2007 2.22E-04 -8.41E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 11 MSChevronPascagoula F-8510

Particulate Matter (PM) filterable Sample #3 11/6/2007 6.38E-04 -7.36E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 12 MSDuPontDeLisle1342

AH-101 (BLR1342)

Particulate Matter (PM) filterable Sample #1 3/14/2008 5.72E-04 -7.47E+00 /Natural gas/ - - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 12 MSDuPontDeLisle1342

AH-101 (BLR1342)

Particulate Matter (PM) filterable Sample #2 3/14/2008 4.15E-04 -7.79E+00 /Natural gas/ - - - - - 

 

YES Gas 1 12 MSDuPontDeLisle1342

AH-101 (BLR1342)

Particulate Matter (PM) filterable Sample #3 3/14/2008 3.61E-04 -7.93E+00 /Natural gas/ - - - - - 

 

YES Gas 1 13 MDUofMaryland EU 001-4

Particulate Matter (PM) filterable Sample #1 2/20/2002 4.98E-04 -7.60E+00 /Natural gas/

YES Gas 1 13 MDUofMaryland EU 001-4

Particulate Matter (PM) filterable Sample #2 2/20/2002 3.98E-04 -7.83E+00 /Natural gas/

YES Gas 1 13 MDUofMaryland EU 001-4

Particulate Matter (PM) filterable Sample #3 2/20/2002 5.98E-04 -7.42E+00 /Natural gas/

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #1 2/28/2007 2.89E-02 -3.54E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #1 5/17/2007 1.00E-03 -6.91E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #1 5/15/2007 6.00E-04 -7.42E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #2 2/28/2007 3.16E-02 -3.45E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #2 5/15/2007 3.10E-03 -5.78E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #2 5/17/2007 1.00E-04 -9.21E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #3 5/15/2007 2.00E-04 -8.52E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 14 TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #3 2/28/2007 2.81E-02 -3.57E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #1 5/15/2007 1.60E-03 -6.44E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #1 5/16/2007 1.50E-03 -6.50E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #1 2/27/2007 1.08E-01 -2.23E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #2 5/15/2007 2.30E-03 -6.07E+00 /Refinery gas/ - - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #2 5/16/2007 1.00E-04 -9.21E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #2 2/27/2007 1.20E-02 -4.42E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #3 5/16/2007 1.00E-04 -9.21E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #3 2/27/2007 1.24E-02 -4.39E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 15 TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #3 5/15/2007 4.80E-03 -5.34E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 16 NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #1 10/11/2007 1.00E-03 -6.91E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 16 NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #2 10/11/2007 3.00E-04 -8.11E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 16 NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #3 10/11/2007 5.00E-04 -7.60E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 17 NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #1 11/14/2007 4.81E-04 -7.64E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 17 NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #2 11/14/2007 4.36E-04 -7.74E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 17 NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #3 11/14/2007 9.50E-04 -6.96E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 18 NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #1 8/27/2008 9.21E-04 -6.99E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 18 NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #2 8/28/2008 7.00E-04 -7.26E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 18 NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #3 8/28/2008 2.48E-04 -8.30E+00 /Refinery gas/ - - - - - 

 

YES Gas 1 y 1 INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable 1 9/25/2009 5.24E-06 -1.22E+01 Natural gas - - - - - 

 

YES Gas 1 y 1 INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable 2 9/26/2009 3.73E-06 -1.25E+01 Natural gas - - - - - 

 

YES Gas 1 y 1 INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable 3 9/26/2009 5.39E-06 -1.21E+01 Natural gas - - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 y 1 INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable Sample #1 9/19/1997 1.40E-02 -4.27E+00 /Natural gas/ - - - - - 

 

YES Gas 1 y 1 INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable Sample #2 9/19/1997 9.90E-03 -4.62E+00 /Natural gas/ - - - - - 

 

YES Gas 1 y 1 INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable Sample #3 9/19/1997 1.53E-02 -4.18E+00 /Natural gas/ - - - - - 

 

YES Gas 1 y 2 INNucorSteel

Cold Mill Annealing

Particulate Matter (PM) filterable M5-1 8/18/2009 1.39E-03 -6.58E+00 Natural gas - - - - - 

 

YES Gas 1 y 2 INNucorSteel

Cold Mill Annealing

Particulate Matter (PM) filterable M5-2 8/18/2009 7.90E-04 -7.14E+00 Natural gas - - - - - 

 

YES Gas 1 y 2 INNucorSteel

Cold Mill Annealing

Particulate Matter (PM) filterable M5-3 8/18/2009 9.28E-04 -6.98E+00 Natural gas - - - - - 

 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801

Particulate Matter (PM) filterable 528-1 8/26/2009 8.21E-04 -7.10E+00

Heavy Recycle/Natural gas/Petrochemical process gas - - - - - 

 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801

Particulate Matter (PM) filterable 528-2 8/26/2009 2.33E-04 -8.36E+00

Heavy Recycle/Natural gas/Petrochemical process gas - - - - - 

 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801

Particulate Matter (PM) filterable 528-3 8/27/2009 2.06E-04 -8.49E+00

Heavy Recycle/Natural gas/Petrochemical process gas - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 8/28/2002 7.20E-03 -4.93E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 8/29/2000 8.10E-03 -4.82E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 9/21/2007 5.50E-04 -7.51E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 7/28/1998 6.00E-03 -5.12E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 8/10/2004 2.61E-02 -3.65E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 11/9/1999 2.65E-02 -3.63E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 2/2/2000 3.18E-03 -5.75E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 10/27/1992 1.00E-02 -4.61E+00 /Coke Oven Gas/ - - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 9/24/1994 1.44E-02 -4.24E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 7/19/2000 3.10E-03 -5.78E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 8/28/2002 6.70E-03 -5.01E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 8/10/2004 3.76E-02 -3.28E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 10/27/1992 1.30E-02 -4.34E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 9/21/2007 1.06E-03 -6.85E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 8/29/2000 2.12E-02 -3.85E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 9/24/1994 1.21E-02 -4.41E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 7/28/1998 1.60E-03 -6.44E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 11/9/1999 2.11E-02 -3.86E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 7/19/2000 2.70E-03 -5.91E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate 

Matter (PM) filterable Sample #2 2/2/2000 3.92E-03 -5.54E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 7/28/1998 2.40E-03 -6.03E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 9/24/1994 2.94E-02 -3.53E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 7/19/2000 7.00E-03 -4.96E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 11/9/1999 2.56E-02 -3.67E+00 /Coke Oven Gas/ - - - - - 

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 9/21/2007 7.60E-04 -7.18E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 8/28/2002 1.02E-02 -4.59E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 8/29/2000 1.40E-03 -6.57E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 8/10/2004 4.21E-02 -3.17E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 2/2/2000 3.92E-03 -5.54E+00 /Coke Oven Gas/ - - - - - 

 

YES Gas 2 2 WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 10/27/1992 1.30E-02 -4.34E+00 /Coke Oven Gas/ - - - - - 

 

YES Liquid 1 TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86

Particulate Matter (PM) filterable 1 11/17/2009 7.19E-04 -7.24E+00 No. 2 Distillate - - - - - 1

 

YES Liquid 1 TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86

Particulate Matter (PM) filterable 2 11/17/2009 4.12E-04 -7.80E+00 No. 2 Distillate - - - - - 1

 

YES Liquid 1 TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86

Particulate Matter (PM) filterable 3 11/18/2009 DLL 4.02E-04 -7.82E+00 No. 2 Distillate - - - - - 1

 

YES Liquid 2 SCGPChemRussellville FO Boiler

Particulate Matter (PM) filterable Sample #1 8/26/2009 8.00E-04 -7.13E+00 Diesel fuel - - - - - 1

 

YES Liquid 2 SCGPChemRussellville FO Boiler

Particulate Matter (PM) filterable Sample #2 8/26/2009 5.00E-04 -7.60E+00 Diesel fuel - - - - - 1

 

YES Liquid 2 SCGPChemRussellville FO Boiler

Particulate Matter (PM) filterable Sample #3 8/26/2009 5.00E-04 -7.60E+00 Diesel fuel - - - - - 1

 

YES Liquid 3 NJSunocoWestville Boiler #8

Particulate Matter (PM) filterable Sample #1 11/20/2007 9.34E-04 -6.98E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 3 NJSunocoWestville Boiler #8

Particulate Matter (PM) filterable Sample #2 11/20/2007 8.82E-05 -9.34E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 3 NJSunocoWestville Boiler #8

Particulate Matter (PM) filterable Sample #3 11/20/2007 1.01E-03 -6.90E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 4 PAConemaughPowerPlantNew Aux Boiler B

Particulate Matter (PM) filterable Sample #1 10/17/2006 1.30E-03 -6.65E+00 /No. 2 Distillate/ - - - - - 1

 

YES Liquid 4 PAConemaughPowerPlantNew Aux Boiler B

Particulate Matter (PM) filterable Sample #2 10/17/2006 3.20E-04 -8.05E+00 /No. 2 Distillate/ - - - - - 1

 

YES Liquid 4 PAConemaughPowerPlantNew Aux Boiler B

Particulate Matter (PM) filterable Sample #3 10/17/2006 1.00E-03 -6.91E+00 /No. 2 Distillate/ - - - - - 1

 

YES Liquid 5 NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #1 11/15/2007 8.01E-04 -7.13E+00 /Jet Fuel/ - - - - - 1

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid 5 NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #2 11/15/2007 9.65E-04 -6.94E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 5 NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #3 11/15/2007 1.30E-03 -6.65E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #1 8/20/2009 1.05E-03 -6.86E+00 Deinking residuals/Natural gas - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #1 9/19/2007 2.90E-03 -5.84E+00 /Deinking Residuals/ - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #1 1/13/1999 1.10E-03 -6.81E+00 /Deinking Residuals/ - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #2 1/13/1999 1.50E-03 -6.50E+00 /Deinking Residuals/ - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #2 9/19/2007 2.60E-03 -5.95E+00 /Deinking Residuals/ - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #2 8/20/2009 1.54E-03 -6.48E+00 Deinking residuals/Natural gas - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #3 1/14/1999 1.10E-03 -6.81E+00 /Deinking Residuals/ - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #3 9/19/2007 2.90E-03 -5.84E+00 /Deinking Residuals/ - - - - 100.00 

 

YES Liquid 6 WIGPGreenBay2818

B10 - Wastepaper Sludge-Fired Boiler 10

Particulate Matter (PM) filterable Sample #3 8/21/2009 1.42E-03 -6.56E+00 Deinking residuals/Natural gas - - - - 100.00 

 

YES Liquid 7 PACherokeePharm

SG-C, Title V Source ID 037

Particulate Matter (PM) filterable Sample #1 5/21/1998 2.00E-03 -6.21E+00 /Natural gas/No. 2 Distillate/

YES Liquid 7 PACherokeePharm

SG-C, Title V Source ID 037

Particulate Matter (PM) filterable Sample #2 5/21/1998 1.30E-03 -6.65E+00 /Natural gas/No. 2 Distillate/

YES Liquid 7 PACherokeePharm

SG-C, Title V Source ID 037

Particulate Matter (PM) filterable Sample #3 5/21/1998 1.50E-03 -6.50E+00 /Natural gas/No. 2 Distillate/

YES Liquid 8 NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #1 12/19/2005 1.95E-03 -6.24E+00 /Jet Fuel/ - - - - - 1

 
Appendix C-4: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid 8 NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #2 12/19/2005 2.07E-03 -6.18E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 8 NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #3 12/19/2005 1.13E-03 -6.79E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 9 PACherokeePharm

SG-B, Title V Source ID 036

Particulate Matter (PM) filterable Sample #1 5/19/1998 2.20E-03 -6.12E+00 /Natural gas/No. 2 Distillate/

YES Liquid 9 PACherokeePharm

SG-B, Title V Source ID 036

Particulate Matter (PM) filterable Sample #2 5/19/1998 2.00E-03 -6.21E+00 /Natural gas/No. 2 Distillate/

YES Liquid 9 PACherokeePharm

SG-B, Title V Source ID 036

Particulate Matter (PM) filterable Sample #3 5/19/1998 1.20E-03 -6.73E+00 /Natural gas/No. 2 Distillate/

YES Liquid 10 NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #1 11/16/2007 2.08E-03 -6.18E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 10 NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #2 11/16/2007 1.23E-03 -6.70E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 10 NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #3 11/16/2007 2.15E-03 -6.14E+00 /Jet Fuel/ - - - - - 1

 

YES Liquid 11 SCMilliken-Dewey D30

Particulate Matter (PM) filterable Sample #1 8/12/2009 4.00E-03 -5.52E+00 Anhydrides Waste - - - - 100.00 

 

YES Liquid 11 SCMilliken-Dewey D30

Particulate Matter (PM) filterable Sample #2 8/12/2009 1.50E-03 -6.50E+00 Anhydrides Waste - - - - 100.00 

 

YES Liquid 11 SCMilliken-Dewey D30

Particulate Matter (PM) filterable Sample #3 8/12/2009 1.00E-03 -6.91E+00 Anhydrides Waste - - - - 100.00 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 1 FLUSSugarCorp Boiler No. 7 Mercury (Hg) Sample #1 1/2/2003 ND 1.15E-07 -1.60E+01 /Bagasse/ 100.00 - - - - 

 

YES Biomass 1 FLUSSugarCorp Boiler No. 7 Mercury (Hg) Sample #2 1/2/2003 ND 9.08E-08 -1.62E+01 /Bagasse/ 100.00 - - - - 

 

YES Biomass 1 FLUSSugarCorp Boiler No. 7 Mercury (Hg) Sample #3 1/2/2003 ND 8.60E-08 -1.63E+01 /Bagasse/ 100.00 - - - - 

 

YES Biomass 2 ORFlakeboardEugene Boiler-2 Mercury (Hg) M29-1 8/26/2009 ND 9.90E-08 -1.61E+01

Natural gas/Wood: Unadulterated Lumber

YES Biomass 2 ORFlakeboardEugene Boiler-2 Mercury (Hg) M29-2 8/27/2009 ND 2.20E-07 -1.53E+01

Natural gas/Wood: Unadulterated Lumber

YES Biomass 2 ORFlakeboardEugene Boiler-2 Mercury (Hg) M29-3 8/27/2009 ND 9.00E-08 -1.62E+01

Natural gas/Wood: Unadulterated Lumber

YES Biomass 3 MESDWarrenSomerset

No2 Power Boiler Mercury (Hg) 1 7/28/2009 DLL 1.98E-07 -1.54E+01

Biomass/Industrial Sludge/No. 2 Distillate/No. 6 Residual oil/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF) - - - 51.78 38.68 

 

YES Biomass 3 MESDWarrenSomerset

No2 Power Boiler Mercury (Hg) 2 7/28/2009 DLL 1.21E-07 -1.59E+01

Biomass/Industrial Sludge/No. 2 Distillate/No. 6 Residual oil/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF) - - - 51.78 38.68 

 

YES Biomass 3 MESDWarrenSomerset

No2 Power Boiler Mercury (Hg) 3 7/28/2009 DLL 1.13E-07 -1.60E+01

Biomass/Industrial Sludge/No. 2 Distillate/No. 6 Residual oil/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF) - - - 51.78 38.68 

 

YES Biomass 3 MESDWarrenSomerset

No2 Power Boiler Mercury (Hg) Sample #1 4/24/2008 3.26E-07 -1.49E+01

/Hog Fuel/No. 6 Residual oil/Wood: Bark/

YES Biomass 3 MESDWarrenSomerset

No2 Power Boiler Mercury (Hg) Sample #2 4/24/2008 3.48E-07 -1.49E+01

/Hog Fuel/No. 6 Residual oil/Wood: Bark/

YES Biomass 3 MESDWarrenSomerset

No2 Power Boiler Mercury (Hg) Sample #3 4/24/2008 3.44E-07 -1.49E+01

/Hog Fuel/No. 6 Residual oil/Wood: Bark/

YES Biomass 4 SCBowaterCoatedPaper

Combination Boiler No. 1 Mercury (Hg) Sample #1 4/21/2004 ND 1.89E-07 -1.55E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 76.48 - 19.62 

 

YES Biomass 4 SCBowaterCoatedPaper

Combination Boiler No. 1 Mercury (Hg) Sample #2 4/21/2004 1.61E-07 -1.56E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 76.48 - 19.62 

 

YES Biomass 5 TNKimberlyClark2397 WB Mercury (Hg) Sample #1 8/4/2005 2.10E-07 -1.54E+01

/Deinking Residuals/Wood: Unadulterated Lumber/

YES Biomass 5 TNKimberlyClark2397 WB Mercury (Hg) Sample #2 8/4/2005 1.90E-07 -1.55E+01

/Deinking Residuals/Wood: Unadulterated Lumber/

YES Biomass 5 TNKimberlyClark2397 WB Mercury (Hg) Sample #3 8/4/2005 1.30E-07 -1.59E+01

/Deinking Residuals/Wood: Unadulterated Lumber/

YES Biomass 6 FLSmurfit-Stone 5PB Mercury (Hg) Sample #1 7/10/2007 2.55E-07 -1.52E+01 /Biomass/No. 6 Residual oil/ - - - 51.85 48.15 

 

YES Biomass 6 FLSmurfit-Stone 5PB Mercury (Hg) Sample #3 7/10/2007 1.54E-07 -1.57E+01 /Biomass/No. 6 Residual oil/ - - - 51.85 48.15 

 

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #1 8/5/2009 ND 7.81E-07 -1.41E+01

Natural gas/No. 6 Residual oil/Wood: Bark

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #1 4/27/2006 3.78E-08 -1.71E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 83.32 - 8.59 

 

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #1 8/5/2009 ND 7.81E-07 -1.41E+01

Natural gas/No. 6 Residual oil/Wood: Bark

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #2 8/6/2009 ND 7.95E-07 -1.40E+01

Natural gas/No. 6 Residual oil/Wood: Bark - - 85.43 - 0.40 

 

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #2 4/27/2006 3.68E-07 -1.48E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 83.32 - 8.59 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #2 8/6/2009 ND 7.95E-07 -1.40E+01

Natural gas/No. 6 Residual oil/Wood: Bark - - 85.43 - 0.40 

 

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #3 4/28/2006 2.26E-07 -1.53E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 83.32 - 8.59 

 

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #3 8/6/2009 ND 7.21E-07 -1.41E+01

Natural gas/No. 6 Residual oil/Wood: Bark - - 85.43 - 0.40 

 

YES Biomass 7 GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler Mercury (Hg) Sample #3 8/6/2009 ND 7.21E-07 -1.41E+01

Natural gas/No. 6 Residual oil/Wood: Bark - - 85.43 - 0.40 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) 1 10/27/2009 BDL 2.46E-07 -1.52E+01

Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 83.68 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) 2 10/27/2009 BDL 2.07E-07 -1.54E+01

Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 83.68 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) 3 10/28/2009 BDL 2.17E-07 -1.53E+01

Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 83.68 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) Sample #1 9/28/2005 4.50E-07 -1.46E+01

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 87.59 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) Sample #1 9/29/2005 4.70E-07 -1.46E+01 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) Sample #2 9/29/2005 6.30E-07 -1.43E+01 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) Sample #2 9/28/2005 7.50E-07 -1.41E+01

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 87.59 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) Sample #3 9/28/2005 6.00E-07 -1.43E+01

/Tire Derived Fuel (TDF)/Wood: Bark/ - - 87.59 - - 

 

YES Biomass 8 KYNewPage-Wickliffe B09 Mercury (Hg) Sample #3 9/29/2005 5.90E-07 -1.43E+01 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 9 NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #1 9/16/1999 ND 2.36E-07 -1.53E+01 /No. 6 Residual oil/Wood: Bark/ - - 31.88 - 68.12 

 

YES Biomass 9 NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #1 9/15/1999 ND 2.64E-07 -1.51E+01 /No. 6 Residual oil/Wood: Bark/ - - 32.38 - 67.62 

 

YES Biomass 9 NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #2 9/20/1999 ND 2.17E-07 -1.53E+01 /No. 6 Residual oil/Wood: Bark/ - - 31.88 - 68.12 

 

YES Biomass 9 NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #2 9/15/1999 ND 2.73E-07 -1.51E+01 /No. 6 Residual oil/Wood: Bark/ - - 32.38 - 67.62 

 

YES Biomass 9 NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #3 9/16/1999 ND 2.69E-07 -1.51E+01 /No. 6 Residual oil/Wood: Bark/ - - 32.38 - 67.62 

 

YES Biomass 10 NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) 1 8/26/2009 DLL 5.56E-07 -1.44E+01 Biomass - - - 100.00 - 

 

YES Biomass 10 NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) 2 8/26/2009 DLL 4.47E-07 -1.46E+01 Biomass - - - 100.00 - 

 

YES Biomass 10 NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) 3 8/27/2009 DLL 5.11E-07 -1.45E+01 Biomass - - - 100.00 - 

 

YES Biomass 10 NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) Sample #1 8/3/2005 2.30E-07 -1.53E+01

/Natural gas/Plant-based Agricultural Residue/

YES Biomass 10 NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) Sample #2 8/3/2005 2.30E-07 -1.53E+01

/Natural gas/Plant-based Agricultural Residue/

YES Biomass 10 NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) Sample #3 8/3/2005 2.30E-07 -1.53E+01

/Natural gas/Plant-based Agricultural Residue/
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 11 SCBowaterCoatedPaper

Combination Boiler No. 2 Mercury (Hg) 1 10/6/2009 BDL 2.79E-07 -1.51E+01

Natural gas/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark - - 95.91 - - 

 

YES Biomass 11 SCBowaterCoatedPaper

Combination Boiler No. 2 Mercury (Hg) 2 10/7/2009 BDL 3.64E-07 -1.48E+01

Natural gas/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark - - 95.91 - - 

 

YES Biomass 11 SCBowaterCoatedPaper

Combination Boiler No. 2 Mercury (Hg) 3 10/7/2009 BDL 9.18E-07 -1.39E+01

Natural gas/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark - - 95.91 - - 

 

YES Biomass 11 SCBowaterCoatedPaper

Combination Boiler No. 2 Mercury (Hg) Sample #1 4/21/2004 2.75E-07 -1.51E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 94.75 - 0.60 

 

YES Biomass 11 SCBowaterCoatedPaper

Combination Boiler No. 2 Mercury (Hg) Sample #2 4/21/2004 2.11E-07 -1.54E+01

/No. 6 Residual oil/Tire Derived Fuel (TDF)/Wood: Bark/ - - 94.75 - 0.60 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) 1 8/4/2009 DLL 6.14E-08 -1.66E+01 Biomass/Coal: Bituminous - 51.03 - 48.97 - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) 2 8/5/2009 DLL 5.99E-08 -1.66E+01 Biomass/Coal: Bituminous - 51.03 - 48.97 - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) 3 8/5/2009 DLL 5.90E-08 -1.66E+01 Biomass/Coal: Bituminous - 51.03 - 48.97 - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #1 2/15/2006 1.26E-08 -1.82E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #1 2/22/2006 3.37E-07 -1.49E+01 /Biomass/Coal: Bituminous/ - 23.18 - 76.82 - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #2 2/21/2006 ND 7.54E-09 -1.87E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #2 2/23/2006 3.77E-07 -1.48E+01 /Biomass/Coal: Bituminous/ - 23.18 - 76.82 - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #3 2/21/2006 2.27E-08 -1.76E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #3 2/23/2006 1.28E-07 -1.59E+01 /Biomass/Coal: Bituminous/ - 23.18 - 76.82 - 

 

YES Coal 2 MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #1 1/10/2007 ND 3.03E-08 -1.73E+01 /Coal: Bituminous/Natural gas/

YES Coal 2 MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #1 1/9/2007 ND 3.71E-08 -1.71E+01 /Coal: Bituminous/Natural gas/

YES Coal 2 MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #2 1/9/2007 ND 3.37E-08 -1.72E+01 /Coal: Bituminous/Natural gas/

YES Coal 2 MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #2 1/10/2007 ND 3.44E-08 -1.72E+01 /Coal: Bituminous/Natural gas/

YES Coal 2 MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #3 1/9/2007 ND 1.52E-08 -1.80E+01 /Coal: Bituminous/Natural gas/

YES Coal 2 MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #3 1/10/2007 ND 3.38E-08 -1.72E+01 /Coal: Bituminous/Natural gas/

YES Coal 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Mercury (Hg) Sample #1 8/26/2009 ND 3.18E-08 -1.73E+01 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Mercury (Hg) Sample #2 8/26/2009 ND 2.80E-08 -1.74E+01 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Mercury (Hg) Sample #3 8/27/2009 5.53E-08 -1.67E+01 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 4 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Mercury (Hg) 1 6/3/2009 6.34E-08 -1.66E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Mercury (Hg) 2 6/3/2009 4.01E-08 -1.70E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Mercury (Hg) 3 6/4/2009 8.15E-08 -1.63E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 5 INPurdueUniverisity Boiler 5 Mercury (Hg) M5-1 7/21/2009 1.14E-07 -1.60E+01 Coal: Bituminous - 100.00 - - - 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 5 INPurdueUniverisity Boiler 5 Mercury (Hg) M5-2 7/21/2009 1.35E-07 -1.58E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 5 INPurdueUniverisity Boiler 5 Mercury (Hg) M5-3 7/22/2009 1.19E-07 -1.59E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 6 ILPolyOne B1 Mercury (Hg) 1 9/9/2009 1.62E-07 -1.56E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 6 ILPolyOne B1 Mercury (Hg) 2 9/9/2009 1.42E-07 -1.58E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 6 ILPolyOne B1 Mercury (Hg) 3 9/10/2009 6.46E-08 -1.66E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 6 ILPolyOne B1 Mercury (Hg) Sample #1 11/14/2006 2.22E-07 -1.53E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #1 7/26/2007 ND 3.96E-07 -1.47E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #1 7/25/2007 ND 1.41E-07 -1.58E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #2 7/26/2007 ND 1.54E-07 -1.57E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #2 7/25/2007 ND 9.27E-08 -1.62E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #3 7/25/2007 ND 1.98E-07 -1.54E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 7 MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #3 7/26/2007 ND 3.07E-07 -1.50E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 8 MNADMCornDivision

Coal Boiler #1 EU049 Mercury (Hg) Sample #2 10/25/2008 1.59E-07 -1.57E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 8 MNADMCornDivision

Coal Boiler #2 EU050 Mercury (Hg) Sample #2 10/25/2008 1.59E-07 -1.57E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #1 11/25/2003 4.50E-07 -1.46E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 57.02 42.98 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #1 8/18/2009 1.28E-07 -1.59E+01 Biomass/Coal: Bituminous - 42.30 - 57.70 - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #1 11/7/2007 8.90E-07 -1.39E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 68.84 31.16 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #1 11/3/2005 2.40E-07 -1.52E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 40.69 59.31 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #2 8/18/2009 1.33E-07 -1.58E+01 Biomass/Coal: Bituminous - 42.30 - 57.70 - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #2 11/25/2003 3.10E-07 -1.50E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 57.02 42.98 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #2 11/7/2007 8.40E-07 -1.40E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 68.84 31.16 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #2 11/3/2005 2.50E-07 -1.52E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 40.69 59.31 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #3 11/25/2003 4.00E-07 -1.47E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 57.02 42.98 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #3 11/7/2007 7.00E-07 -1.42E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 68.84 31.16 - - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #3 8/19/2009 2.50E-07 -1.52E+01 Biomass/Coal: Bituminous - 42.30 - 57.70 - 

 

YES Coal 10 SCCogenSouth

B001 - Main Boiler Mercury (Hg) Sample #3 11/3/2005 2.10E-07 -1.54E+01

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 40.69 59.31 - - 

 

YES Coal 11 NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Mercury (Hg) Sample #1 8/18/2009 ND 1.68E-07 -1.56E+01

Coal: Bituminous/Hog Fuel/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Used Petroleum-based Oils - 21.27 - 78.47 0.26 

 

YES Coal 11 NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Mercury (Hg) Sample #1 3/25/2008 ND 2.01E-06 -1.31E+01

/Coal: Bituminous/Hog Fuel/No. 6 Residual oil/ - 48.01 - 51.99 - 

 

YES Coal 11 NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Mercury (Hg) Sample #2 8/18/2009 ND 1.81E-07 -1.55E+01

Coal: Bituminous/Hog Fuel/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Used Petroleum-based Oils - 21.27 - 78.47 0.26 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 11 NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Mercury (Hg) Sample #2 3/25/2008 ND 1.87E-06 -1.32E+01

/Coal: Bituminous/Hog Fuel/No. 6 Residual oil/ - 48.01 - 51.99 - 

 

YES Coal 11 NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Mercury (Hg) Sample #3 8/26/2009 ND 1.85E-07 -1.55E+01

Coal: Bituminous/Hog Fuel/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Used Petroleum-based Oils - 21.27 - 78.47 0.26 

 

YES Coal 11 NCDomtar

65-25-0310 (No. 2 Hog Fuel Boiler) Mercury (Hg) Sample #3 3/25/2008 ND 1.97E-06 -1.31E+01

/Coal: Bituminous/Hog Fuel/No. 6 Residual oil/ - 48.01 - 51.99 - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) 1 7/22/2009 DLL 2.70E-07 -1.51E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) 2 7/22/2009 DLL 1.22E-07 -1.59E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) 3 7/23/2009 DLL 1.61E-07 -1.56E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #1 6/13/2007 ND 7.28E-07 -1.41E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #1 6/14/2007 ND 1.86E-07 -1.55E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #2 6/14/2007 ND 6.84E-07 -1.42E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #2 6/13/2007 ND 2.36E-07 -1.53E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #3 6/14/2007 ND 9.84E-07 -1.38E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 12 MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #3 6/15/2007 1.22E-07 -1.59E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 13 IAMonsantoMuscatine

Boiler #8 (EP195) Mercury (Hg) Sample #1 10/15/2009 1.11E-07 -1.60E+01

Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue - 61.99 - 9.40 28.61 

 

YES Coal 13 IAMonsantoMuscatine

Boiler #8 (EP195) Mercury (Hg) Sample #2 10/16/2009 3.29E-07 -1.49E+01

Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue - 61.99 - 9.40 28.61 

 

YES Coal 13 IAMonsantoMuscatine

Boiler #8 (EP195) Mercury (Hg) Sample #3 10/16/2009 2.45E-07 -1.52E+01

Coal: Bituminous/Industrial Sludge/Plant-based Agricultural Residue - 61.99 - 9.40 28.61 

 

YES Coal 14 NCTysonHarmony TYS-ES-21 Mercury (Hg) Sample #1 9/25/2006 2.70E-07 -1.51E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 14 NCTysonHarmony TYS-ES-21 Mercury (Hg) Sample #2 9/26/2006 2.50E-07 -1.52E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 14 NCTysonHarmony TYS-ES-21 Mercury (Hg) Sample #3 9/27/2006 2.10E-07 -1.54E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 15

IDAmalgamatedSugarCoTwinFalls S-B1 Mercury (Hg) Sample #1 9/26/2006 2.41E-07 -1.52E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 15

IDAmalgamatedSugarCoTwinFalls S-B1 Mercury (Hg) Sample #2 9/26/2006 2.50E-07 -1.52E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 15

IDAmalgamatedSugarCoTwinFalls S-B1 Mercury (Hg) Sample #3 9/26/2006 2.76E-07 -1.51E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #1 10/4/2006 2.60E-06 -1.29E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #1 5/3/2006 1.65E-06 -1.33E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #1 9/14/2006 1.98E-07 -1.54E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #2 5/3/2006 1.02E-06 -1.38E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #2 9/14/2006 3.01E-07 -1.50E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #2 10/4/2006 3.19E-06 -1.27E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #3 10/4/2006 2.98E-06 -1.27E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #3 5/3/2006 9.64E-07 -1.39E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 16 VAStanleyFurniture FB-2 Mercury (Hg) Sample #3 9/14/2006 3.69E-07 -1.48E+01

/Coal: Bituminous/Wood: Plywood, Particleboard (containing glues or resins)/Wood: Unadulterated Lumber/

YES Coal 17 GASPNewsprint PB2 Mercury (Hg) 1 8/25/2009 BDL 1.17E-07 -1.60E+01

Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF) - 30.00 - - 50.03 

 

YES Coal 17 GASPNewsprint PB2 Mercury (Hg) 2 8/26/2009 BDL 3.45E-07 -1.49E+01

Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF) - 30.00 - - 50.03 

 

YES Coal 17 GASPNewsprint PB2 Mercury (Hg) 3 8/26/2009 BDL 4.19E-07 -1.47E+01

Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF) - 30.00 - - 50.03 

 

YES Coal 18 MENewPage-Rumford Cogen#6 Mercury (Hg) 1 12/8/2009 DLL 9.18E-07 -1.39E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 18 MENewPage-Rumford Cogen#6 Mercury (Hg) 2 12/8/2009 DLL 6.80E-07 -1.42E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 18 MENewPage-Rumford Cogen#6 Mercury (Hg) 3 12/9/2009 DLL 8.69E-07 -1.40E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 18 MENewPage-Rumford Cogen#6 Mercury (Hg) Sample #1 11/25/2003 4.69E-07 -1.46E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 MENewPage-Rumford Cogen#6 Mercury (Hg) Sample #1 11/25/2003 2.96E-07 -1.50E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 MENewPage-Rumford Cogen#7 Mercury (Hg) 1 12/8/2009 DLL 9.18E-07 -1.39E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 18 MENewPage-Rumford Cogen#7 Mercury (Hg) 2 12/8/2009 DLL 6.80E-07 -1.42E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 18 MENewPage-Rumford Cogen#7 Mercury (Hg) 3 12/9/2009 DLL 8.69E-07 -1.40E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

 

YES Coal 18 MENewPage-Rumford Cogen#7 Mercury (Hg) Sample #1 11/25/2003 4.69E-07 -1.46E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.27 - 49.86 2.03 

 

YES Coal 18 MENewPage-Rumford Cogen#7 Mercury (Hg) Sample #1 11/25/2003 2.96E-07 -1.50E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 33.27 - 49.86 2.03 

 

YES Coal 20 AKDoyonUtilities_AK 4 Mercury (Hg) Sample #1 8/17/2005 3.36E-07 -1.49E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 AKDoyonUtilities_AK 4 Mercury (Hg) Sample #2 8/17/2005 4.12E-07 -1.47E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 AKDoyonUtilities_AK 4 Mercury (Hg) Sample #3 8/17/2005 3.07E-07 -1.50E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 21 IAADMCornProcessingCR EU-501B Mercury (Hg) Sample #1 8/12/2009 8.18E-08 -1.63E+01

Coal: Bituminous/Coal: Subbituminous - 100.00 - - - 

 

YES Coal 21 IAADMCornProcessingCR EU-501B Mercury (Hg) Sample #2 8/13/2009 2.96E-07 -1.50E+01

Coal: Bituminous/Coal: Subbituminous - 100.00 - - - 

 

YES Coal 21 IAADMCornProcessingCR EU-501B Mercury (Hg) Sample #3 8/13/2009 6.97E-07 -1.42E+01

Coal: Bituminous/Coal: Subbituminous - 100.00 - - - 

 

YES Coal 22 VAUniversityofVirginia 7103-1-01R Mercury (Hg) M29-1 9/17/2009 < 3.61E-07 -1.48E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 22 VAUniversityofVirginia 7103-1-01R Mercury (Hg) M29-2 9/17/2009 < 3.81E-07 -1.48E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 22 VAUniversityofVirginia 7103-1-01R Mercury (Hg) M29-3 9/18/2009 < 3.67E-07 -1.48E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 23 VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #1 5/25/2005 5.07E-06 -1.22E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #1 11/23/2004 ND 6.17E-07 -1.43E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #2 11/24/2004 2.78E-07 -1.51E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #2 5/25/2005 4.22E-06 -1.24E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #3 5/25/2005 4.02E-06 -1.24E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 23 VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #3 11/24/2004 2.54E-07 -1.52E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 24 MNVersoPaper EU006 B&W Mercury (Hg) M29-1 8/25/2009 BDL 9.99E-07 -1.38E+01

Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/Wood: Bark - 70.22 20.13 - 2.26 

 

YES Coal 24 MNVersoPaper EU006 B&W Mercury (Hg) M29-2 8/25/2009 BDL 9.53E-07 -1.39E+01

Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/Wood: Bark - 70.22 20.13 - 2.26 

 

YES Coal 24 MNVersoPaper EU006 B&W Mercury (Hg) M29-3 8/26/2009 BDL 9.41E-07 -1.39E+01

Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/Wood: Bark - 70.22 20.13 - 2.26 

 

YES Coal 24 MNVersoPaper EU006 B&W Mercury (Hg) Sample #1 5/12/2004 3.88E-07 -1.48E+01

/Biomass/Coal: Bituminous/Industrial Sludge/Tire Derived Fuel (TDF)/ - 74.98 - 20.79 3.18 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #1 8/2/2006 1.46E-06 -1.34E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #1 8/1/2006 1.19E-06 -1.36E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #1 7/25/2006 4.30E-07 -1.47E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #2 8/1/2006 8.46E-07 -1.40E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #2 8/2/2006 9.98E-07 -1.38E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #2 7/25/2006 4.17E-07 -1.47E+01 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #3 7/25/2006 3.34E-07 -1.49E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #3 8/1/2006 1.09E-06 -1.37E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #3 8/2/2006 1.14E-06 -1.37E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 26 OHAppletonIdeas

Boiler 4 (B003) Mercury (Hg) Sample #1 1/31/2003 3.66E-07 -1.48E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 26 OHAppletonIdeas

Boiler 4 (B003) Mercury (Hg) Sample #2 1/31/2003 4.03E-07 -1.47E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 26 OHAppletonIdeas

Boiler 4 (B003) Mercury (Hg) Sample #3 1/31/2003 4.13E-07 -1.47E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27 TNNissanSmyrna Boiler 3 Mercury (Hg) Sample #1 3/3/2007 5.00E-07 -1.45E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27 TNNissanSmyrna Boiler 3 Mercury (Hg) Sample #2 3/3/2007 3.00E-07 -1.50E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27 TNNissanSmyrna Boiler 3 Mercury (Hg) Sample #3 3/3/2007 4.50E-07 -1.46E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) M5/29-1BH 8/10/2009 < 6.45E-07 -1.43E+01 Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) M5/29-1FH 8/10/2009 < 5.86E-08 -1.67E+01 Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) M5/29-2BH 8/11/2009 < 8.10E-07 -1.40E+01 Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) M5/29-2FH 8/11/2009 < 8.31E-08 -1.63E+01 Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) M5/29-3BH 8/11/2009 < 8.29E-07 -1.40E+01 Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) M5/29-3FH 8/11/2009 < 8.50E-08 -1.63E+01 Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) Sample #1 11/25/2003 ND 1.00E-06 -1.38E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) Sample #2 11/25/2003 ND 1.10E-06 -1.37E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 28 NCUNCCogen ES-001 Mercury (Hg) Sample #3 11/25/2003 ND 1.20E-06 -1.36E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 INTateLyleSagamore 31B1 Mercury (Hg) M29-1 9/1/2009 4.06E-07 -1.47E+01 Coal: Bituminous/Corn Starch - 97.94 - 2.06 - 

 

YES Coal 29 INTateLyleSagamore 31B1 Mercury (Hg) M29-2 9/2/2009 4.49E-07 -1.46E+01 Coal: Bituminous/Corn Starch - 97.94 - 2.06 - 

 

YES Coal 29 INTateLyleSagamore 31B1 Mercury (Hg) M29-3 9/3/2009 4.40E-07 -1.46E+01 Coal: Bituminous/Corn Starch - 97.94 - 2.06 - 

 

YES Coal 30 OKGPMuskogeeMill B-3 Mercury (Hg) Sample #1 5/20/2003 4.00E-07 -1.47E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 30 OKGPMuskogeeMill B-3 Mercury (Hg) Sample #2 5/20/2003 4.00E-07 -1.47E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 30 OKGPMuskogeeMill B-3 Mercury (Hg) Sample #3 5/20/2003 6.00E-07 -1.43E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 31 TNCargillMemphis

Stoker Boiler 8001 Mercury (Hg) 1 8/5/2009 DLL 4.10E-07 -1.47E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 31 TNCargillMemphis

Stoker Boiler 8001 Mercury (Hg) 2 11/6/2009 DLL 5.60E-07 -1.44E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 31 TNCargillMemphis

Stoker Boiler 8001 Mercury (Hg) 3 8/6/2009 DLL 4.30E-07 -1.47E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 32 WIWausauRhine B26 Mercury (Hg) Sample #1 9/5/2007 7.20E-07 -1.41E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 WIWausauRhine B26 Mercury (Hg) Sample #2 9/5/2007 3.30E-07 -1.49E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 WIWausauRhine B26 Mercury (Hg) Sample #3 9/5/2007 3.90E-07 -1.48E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ALIPCourtland

No.2 Combination Boiler / 11CU201 Mercury (Hg) Sample #1 9/10/1996 5.64E-07 -1.44E+01

/Coal: Bituminous/Natural gas/Noncondensable Gas (includes stripper offgas)/Wood: Bark/
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 33 ALIPCourtland

No.2 Combination Boiler / 11CU201 Mercury (Hg) Sample #2 9/10/1996 4.84E-07 -1.45E+01

/Coal: Bituminous/Natural gas/Noncondensable Gas (includes stripper offgas)/Wood: Bark/

YES Coal 33 ALIPCourtland

No.2 Combination Boiler / 11CU201 Mercury (Hg) Sample #3 9/10/1996 5.66E-07 -1.44E+01

/Coal: Bituminous/Natural gas/Noncondensable Gas (includes stripper offgas)/Wood: Bark/

YES Coal 34 VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #1 10/12/2004 7.88E-07 -1.41E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #1 10/12/2004 2.50E-06 -1.29E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #2 10/12/2004 4.60E-07 -1.46E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #2 10/12/2004 1.91E-06 -1.32E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #3 10/12/2004 2.30E-06 -1.30E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #3 10/12/2004 3.70E-07 -1.48E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 35 TNNissanSmyrna Boiler 2 Mercury (Hg) Sample #1 3/2/2007 8.00E-07 -1.40E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 35 TNNissanSmyrna Boiler 2 Mercury (Hg) Sample #2 3/2/2007 5.20E-07 -1.45E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 35 TNNissanSmyrna Boiler 2 Mercury (Hg) Sample #3 3/2/2007 3.20E-07 -1.50E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Gas 1 1 NCCampLejeuneMCB

C-AS-4151-16 Mercury (Hg) Sample #1 9/30/2009 9.94E-08 -1.61E+01 Natural gas - - - - - 

 

YES Gas 1 1 NCCampLejeuneMCB

C-AS-4151-16 Mercury (Hg) Sample #2 10/1/2009 9.16E-08 -1.62E+01 Natural gas - - - - - 

 

YES Gas 1 1 NCCampLejeuneMCB

C-AS-4151-16 Mercury (Hg) Sample #3 10/1/2009 8.95E-08 -1.62E+01 Natural gas - - - - - 

 

YES Gas 1 2 CAConocoPhilipsLosAng

D146 B-202 U90 Mercury (Hg) Sample #1 4/23/1995 1.37E-07 -1.58E+01 /Refinery gas/ - - - - - 

 

YES Gas 1 2 CAConocoPhilipsLosAng

D146 B-202 U90 Mercury (Hg) Sample #2 4/24/1995 1.65E-07 -1.56E+01 /Refinery gas/ - - - - - 

 

YES Gas 1 2 CAConocoPhilipsLosAng

D146 B-202 U90 Mercury (Hg) Sample #3 4/25/1995 6.11E-08 -1.66E+01 /Refinery gas/ - - - - - 

 

YES Gas 1 y 1 ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Mercury (Hg) Sample #1 8/26/2009 6.28E-08 -1.66E+01 Natural gas - - - - - 

 

YES Gas 1 y 1 ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Mercury (Hg) Sample #2 8/27/2009 2.47E-08 -1.75E+01 Natural gas - - - - - 

 

YES Gas 1 y 1 ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Mercury (Hg) Sample #3 8/28/2009 1.20E-08 -1.82E+01 Natural gas - - - - - 

 

YES Gas 2 1 SCBMWManufacturingCo HB03 Mercury (Hg) 1 8/25/2009 DLL 1.03E-07 -1.61E+01 Landfill Gas - - - - - 

 

YES Gas 2 1 SCBMWManufacturingCo HB03 Mercury (Hg) 2 8/25/2009 DLL 6.83E-08 -1.65E+01 Landfill Gas - - - - - 

 

YES Gas 2 1 SCBMWManufacturingCo HB03 Mercury (Hg) 3 8/26/2009 DLL 7.61E-08 -1.64E+01 Landfill Gas - - - - - 

 

YES Liquid 1 MNGPDuluth

EU33 Boiler #3 Mercury (Hg) 1 9/10/2009 DLL 9.66E-08 -1.62E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 1 MNGPDuluth

EU33 Boiler #3 Mercury (Hg) 2 9/10/2009 DLL 4.34E-08 -1.70E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 1 MNGPDuluth

EU33 Boiler #3 Mercury (Hg) 3 9/10/2009 DLL 3.59E-08 -1.71E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 2 MEFPLEnergyWyman Unit #5 Mercury (Hg) PM/TM-R1 10/5/2009 8.92E-08 -1.62E+01 No. 6 Residual oil - - - - 100.00 

 
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid 2 MEFPLEnergyWyman Unit #5 Mercury (Hg) PM/TM-R2 10/5/2009 1.05E-07 -1.61E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 2 MEFPLEnergyWyman Unit #5 Mercury (Hg) PM/TM-R3 10/6/2009 6.35E-08 -1.66E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 3 ILCognisCorp Boiler #1 Mercury (Hg) Sample #1 9/16/2009 1.32E-07 -1.58E+01 Bio liquids/Natural gas - - - - - 

 

YES Liquid 3 ILCognisCorp Boiler #1 Mercury (Hg) Sample #2 9/17/2009 1.00E-07 -1.61E+01 Bio liquids/Natural gas - - - - - 

 

YES Liquid 3 ILCognisCorp Boiler #1 Mercury (Hg) Sample #3 9/17/2009 8.66E-08 -1.63E+01 Bio liquids/Natural gas - - - - - 

 

YES Liquid 5 PABoeingRidleyPark 033 Mercury (Hg) M29-1 9/22/2009 DLL 1.37E-07 -1.58E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 5 PABoeingRidleyPark 033 Mercury (Hg) M29-2 9/23/2009 DLL 1.04E-07 -1.61E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 5 PABoeingRidleyPark 033 Mercury (Hg) M29-3 9/24/2009 DLL 1.24E-07 -1.59E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 6

NYConEd59thStStationNewYork Boiler 118 Mercury (Hg) 29-1 9/19/2009 1.57E-07 -1.57E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 6

NYConEd59thStStationNewYork Boiler 118 Mercury (Hg) 29-2 9/19/2009 1.38E-07 -1.58E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 6

NYConEd59thStStationNewYork Boiler 118 Mercury (Hg) 29-3 9/19/2009 1.23E-07 -1.59E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 7 SCMilliken-Dewey D30 Mercury (Hg) Sample #1 8/12/2009 ND 2.80E-07 -1.51E+01 Anhydrides Waste - - - - 100.00 

 

YES Liquid 7 SCMilliken-Dewey D30 Mercury (Hg) Sample #2 8/12/2009 ND 3.40E-07 -1.49E+01 Anhydrides Waste - - - - 100.00 

 

YES Liquid 7 SCMilliken-Dewey D30 Mercury (Hg) Sample #3 8/12/2009 ND 3.40E-07 -1.49E+01 Anhydrides Waste - - - - 100.00 

 

YES Liquid 8

NJVinelandMuniElectricHowardDown Unit 9 Mercury (Hg) 1 7/20/2009 DLL 3.87E-07 -1.48E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 8

NJVinelandMuniElectricHowardDown Unit 9 Mercury (Hg) 2 7/20/2009 DLL 4.10E-07 -1.47E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 8

NJVinelandMuniElectricHowardDown Unit 9 Mercury (Hg) 3 7/21/2009 DLL 3.66E-07 -1.48E+01 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 10 CTElectric Boat EMU 17 Mercury (Hg) 1 8/18/2009 DLL 7.56E-08 -1.64E+01 No. 4 Fuel oil - - - - - 1

 

YES Liquid 10 CTElectric Boat EMU 17 Mercury (Hg) 3 8/19/2009 BDL 7.61E-08 -1.64E+01 No. 4 Fuel oil - - - - - 1

 

YES Liquid 10 CTElectric Boat EMU 17 Mercury (Hg) 4 8/19/2009 DLL 7.68E-08 -1.64E+01 No. 4 Fuel oil - - - - - 1

 

YES Liquid 12 INUSSteelGaryWorks O4B10459 Mercury (Hg) M29-1 9/9/2009 7.59E-07 -1.41E+01

Blast Furnace Gas/Natural gas/No. 6 Residual oil - - - - 13.43 

 

YES Liquid 12 INUSSteelGaryWorks O4B10459 Mercury (Hg) M29-2 9/10/2009 1.33E-07 -1.58E+01

Blast Furnace Gas/Natural gas/No. 6 Residual oil - - - - 13.43 

 

YES Liquid 12 INUSSteelGaryWorks O4B10459 Mercury (Hg) M29-3 9/11/2009 1.45E-06 -1.34E+01

Blast Furnace Gas/Natural gas/No. 6 Residual oil - - - - 13.43 

 

YES Liquid 13

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) 1 11/17/2009 DLL 7.65E-08 -1.64E+01 No. 2 Distillate - - - - - 1

 

YES Liquid 13

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) 2 11/17/2009 DLL 6.56E-08 -1.65E+01 No. 2 Distillate - - - - - 1

 

YES Liquid 13

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) 3 11/18/2009 DLL 6.92E-08 -1.65E+01 No. 2 Distillate - - - - - 1

 

YES Liquid CTElectric Boat EMU 17 Mercury (Hg) Sample #1 4.36E-07 -1.46E+01 No. 4 Fuel oil

YES Liquid CTElectric Boat EMU 18 Mercury (Hg) Sample #1 4.36E-07 -1.46E+01 No. 4 Fuel oil

YES Liquid ILCognisCorp Boiler #1 Mercury (Hg) Sample #1 ND 1.09E-07 -1.60E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Mercury (Hg) Sample #1 ND 1.09E-07 -1.60E+01

Animal Fat/Oils/Tallow/Vegetable Oil
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #1 ND 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #1 3.10E-07 -1.50E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #1 6.14E-07 -1.43E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #10 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #11 ND 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #12 ND 2.57E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #2 ND 2.55E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #2 ND 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #2 1.01E-06 -1.38E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #3 ND 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #3 ND 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #3 1.03E-06 -1.38E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #4 4.62E-07 -1.46E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #5 4.60E-07 -1.46E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package 

Boiler Mercury (Hg) Sample #6 3.07E-07 -1.50E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #7 ND 2.57E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #8 3.07E-07 -1.50E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #9 ND 2.56E-07 -1.52E+01

No. 2 Distillate/No. 6 Residual oil/Used Petroleum-based Oils (onspec)/

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-2, Source #27-0010-28 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I6A-1, Source #27-0010-15 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

I7A-1, Source #27-0010-16 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-1, Source #27-0010-31 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

J107A-2, Source #27-0010-31 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K102L-1, Source #27-0010-42 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-1, Source #27-0010-19 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K300A-2, Source #27-0010-19 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-2, Source #27-0010-83 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-1, Source #27-0010-21 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

S101A-2, Source #27-0010-21 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-1, Source #27-0010-84 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

T116A-2, Source #27-0010-84 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

V1L-1, Source #27-0010-46 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-1, Source #27-0010-29 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-2, Source #27-0010-29 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #1 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #10 ND 2.09E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #11 ND 2.10E-06 -1.31E+01 No. 2 Distillate
Appendix C-5: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #12 ND 2.10E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #2 ND 2.15E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #3 ND 2.13E-06 -1.31E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #4 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #5 ND 2.16E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #6 ND 2.25E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #7 ND 2.17E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #8 ND 2.19E-06 -1.30E+01 No. 2 Distillate

YES Liquid

TNMilanArmyAmmunitionPlant

X21L-3, Source #27-0010-29 Mercury (Hg) Sample #9 ND 2.23E-06 -1.30E+01 No. 2 Distillate
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 1 ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) 1 9/8/2009 < 3.61E-06 -1.25E+01 Hog Fuel - - - 100.00 - 

 

YES Biomass 1 ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) 2 9/8/2009 < 3.69E-06 -1.25E+01 Hog Fuel - - - 100.00 - 

 

YES Biomass 1 ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) 3 9/8/2009 < 3.78E-06 -1.25E+01 Hog Fuel - - - 100.00 - 

 

YES Biomass 1 ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) Sample #1 8/8/2006 8.00E-04 -7.13E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 1 ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) Sample #2 8/8/2006 2.10E-03 -6.17E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 1 ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride 

(HCl) Sample #3 9/8/2006 1.80E-03 -6.32E+00 /Hog Fuel/ - - - 100.00 - 

 

YES Biomass 2 TXDibollTemple-Inland PB-44

Hydrogen Chloride (HCl) Sample #1 6/29/2007 ND 2.50E-05 -1.06E+01

/Wood: Plywood, Particleboard (containing glues or resins)/ - - - 100.00 - 

 

YES Biomass 2 TXDibollTemple-Inland PB-44

Hydrogen Chloride (HCl) Sample #2 6/29/2007 ND 2.50E-05 -1.06E+01

/Wood: Plywood, Particleboard (containing glues or resins)/ - - - 100.00 - 

 

YES Biomass 2 TXDibollTemple-Inland PB-44

Hydrogen Chloride (HCl) Sample #3 6/29/2007 ND 2.50E-05 -1.06E+01

/Wood: Plywood, Particleboard (containing glues or resins)/ - - - 100.00 - 

 

YES Biomass 3 IDPotlatch PB-1 CE

Hydrogen Chloride (HCl) Sample #1 7/28/2009 ND 2.80E-05 -1.05E+01 Hog Fuel - - - 100.00 - 

 

YES Biomass 3 IDPotlatch PB-1 CE

Hydrogen Chloride (HCl) Sample #2 7/28/2009 ND 2.80E-05 -1.05E+01 Hog Fuel - - - 100.00 - 

 

YES Biomass 3 IDPotlatch PB-1 CE

Hydrogen Chloride (HCl) Sample #3 7/28/2009 ND 2.90E-05 -1.04E+01 Hog Fuel - - - 100.00 - 

 

YES Biomass 4 MESDWarrenSomerset

No2 Power Boiler

Hydrogen Chloride (HCl) 2 7/30/2009 5.86E-04 -7.44E+00

Biomass/Industrial Sludge/No. 2 Distillate/No. 6 Residual oil/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF) - - - 51.78 38.68 

 

YES Biomass 4 MESDWarrenSomerset

No2 Power Boiler

Hydrogen Chloride (HCl) 3 7/30/2009 5.39E-04 -7.53E+00

Biomass/Industrial Sludge/No. 2 Distillate/No. 6 Residual oil/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF) - - - 51.78 38.68 

 

YES Biomass 4 MESDWarrenSomerset

No2 Power Boiler

Hydrogen Chloride (HCl) Sample #1 4/18/2008 6.09E-05 -9.71E+00

/Hog Fuel/No. 6 Residual oil/Wood: Bark/

YES Biomass 4 MESDWarrenSomerset

No2 Power Boiler

Hydrogen Chloride (HCl) Sample #2 4/18/2008 5.87E-05 -9.74E+00

/Hog Fuel/No. 6 Residual oil/Wood: Bark/

YES Biomass 5 GAGPMadisonPly

800 Wood Waste Boiler

Hydrogen Chloride (HCl) Sample #1 8/13/2009 9.00E-05 -9.32E+00 Wood: Bark - - 100.00 - - 

 

YES Biomass 5 GAGPMadisonPly

800 Wood Waste Boiler

Hydrogen Chloride 

(HCl) Sample #2 8/13/2009 1.20E-04 -9.03E+00 Wood: Bark - - 100.00 - - 

 

YES Biomass 5 GAGPMadisonPly

800 Wood Waste Boiler

Hydrogen Chloride (HCl) Sample #3 8/14/2009 ND 4.00E-05 -1.01E+01 Wood: Bark - - 100.00 - - 

 

YES Biomass 6 WABoisePaperWallula

Hog Fuel Boiler

Hydrogen Chloride (HCl) Sample #1 5/6/2008 8.67E-05 -9.35E+00

/Hog Fuel/Natural gas/Noncondensable Gas (includes stripper offgas)/
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 6 WABoisePaperWallula

Hog Fuel Boiler

Hydrogen Chloride (HCl) Sample #2 5/6/2008 1.62E-04 -8.73E+00

/Hog Fuel/Natural gas/Noncondensable Gas (includes stripper offgas)/

YES Biomass 6 WABoisePaperWallula

Hog Fuel Boiler

Hydrogen Chloride (HCl) Sample #3 5/6/2008 ND 1.93E-05 -1.09E+01

/Hog Fuel/Natural gas/Noncondensable Gas (includes stripper offgas)/

YES Biomass 7 SCMarlboroPaper

Hogged Fuel Boiler

Hydrogen Chloride (HCl) Sample #1 7/14/2009 ND 1.00E-04 -9.21E+00

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - 

 

YES Biomass 7 SCMarlboroPaper

Hogged Fuel Boiler

Hydrogen Chloride (HCl) Sample #2 7/14/2009 ND 1.00E-04 -9.21E+00

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - 

 

YES Biomass 7 SCMarlboroPaper

Hogged Fuel Boiler

Hydrogen Chloride (HCl) Sample #3 7/14/2009 ND 1.00E-04 -9.21E+00

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - 

 

YES Biomass 8 MEBoralexStratton Boiler #1

Hydrogen Chloride (HCl) Sample #1 10/21/2009 1.34E-04 -8.92E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 8 MEBoralexStratton Boiler #1

Hydrogen Chloride (HCl) Sample #2 10/21/2009 1.34E-04 -8.92E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 8 MEBoralexStratton Boiler #1

Hydrogen Chloride (HCl) Sample #3 10/21/2009 1.34E-04 -8.92E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 9 OHSmurfitCoshocton B006

Hydrogen Chloride (HCl) Sample #1 8/12/2003 1.56E-04 -8.76E+00

/Natural gas/Hydro pulper refuse/Industrial Sludge//Wood: Unadulterated Lumber

YES Biomass 9 OHSmurfitCoshocton B006

Hydrogen Chloride (HCl) Sample #2 8/12/2003 1.49E-04 -8.81E+00

/Natural gas/Hydro pulper refuse/Industrial Sludge//Wood: Unadulterated Lumber

YES Biomass 9 OHSmurfitCoshocton B006

Hydrogen Chloride (HCl) Sample #3 8/12/2003 1.61E-04 -8.74E+00

/Natural gas/Hydro pulper refuse/Industrial Sludge//Wood: Unadulterated Lumber

YES Biomass 10 MTPlumCreek

Wellons Plywood

Hydrogen Chloride (HCl) 1 10/5/2009 BDL 1.54E-04 -8.78E+00

Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)

YES Biomass 10 MTPlumCreek

Wellons Plywood

Hydrogen Chloride (HCl) 2 10/6/2009 BDL 1.68E-04 -8.69E+00

Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)

YES Biomass 10 MTPlumCreek

Wellons Plywood

Hydrogen Chloride (HCl) 3 10/6/2009 BDL 1.69E-04 -8.69E+00

Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)

YES Biomass 11 FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #1 1/19/2005 1.55E-03 -6.47E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 11 FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #1 12/16/2002 2.32E-04 -8.37E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 11 FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #2 12/16/2002 2.15E-04 -8.44E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 11 FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #2 1/19/2005 1.69E-03 -6.38E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 11 FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #3 1/19/2005 1.22E-03 -6.71E+00 /Bagasse/ 100.00 - - - - 

 

YES Biomass 11 FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #3 12/16/2002 1.51E-04 -8.80E+00 /Bagasse/ 100.00 - - - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass 12 ARAnthonyForestProducts SN-12

Hydrogen Chloride (HCl) Sample #1 9/1/2009 2.10E-04 -8.47E+00

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 12 ARAnthonyForestProducts SN-12

Hydrogen Chloride (HCl) Sample #2 9/1/2009 2.30E-04 -8.38E+00

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 12 ARAnthonyForestProducts SN-12

Hydrogen Chloride (HCl) Sample #3 9/2/2009 1.60E-04 -8.74E+00

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #1 8/14/2009 2.00E-04 -8.52E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #1 8/14/2009 3.20E-02 -3.44E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #1 6/22/2006 6.43E-02 -2.74E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #2 8/14/2009 2.60E-02 -3.65E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #2 8/14/2009 2.00E-04 -8.52E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #2 6/22/2006 4.84E-02 -3.03E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #3 6/22/2006 2.22E-02 -3.81E+00 /Wood: Bark/ - - 100.00 - - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #3 8/14/2009 1.80E-02 -4.02E+00 Hog Fuel - - - 100.00 - 

 

YES Biomass 12 WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #3 8/14/2009 2.00E-04 -8.52E+00 Hog Fuel - - - 100.00 - 

 

YES Coal 1 INAlcoaWarrick Unit #3

Hydrogen Chloride (HCl) Sample #1 8/7/2008 ND 1.43E-05 -1.12E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 1 INAlcoaWarrick Unit #3

Hydrogen Chloride (HCl) Sample #2 8/7/2008 ND 1.57E-05 -1.11E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 2 IDTASCOPaul

Erie City Boiler

Hydrogen Chloride (HCl) Sample #1 6/20/2006 ND 3.96E-05 -1.01E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 2 IDTASCOPaul

Erie City Boiler

Hydrogen Chloride (HCl) Sample #2 6/20/2006 ND 4.02E-05 -1.01E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 2 IDTASCOPaul

Erie City Boiler

Hydrogen Chloride 

(HCl) Sample #3 6/21/2006 ND 3.58E-05 -1.02E+01 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 3 INAlcoaWarrick Unit #2

Hydrogen Chloride (HCl) Sample #1 8/6/2008 ND 1.51E-05 -1.11E+01 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 3 INAlcoaWarrick Unit #2

Hydrogen Chloride (HCl) Sample #2 8/6/2008 1.03E-04 -9.18E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 4 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

Hydrogen Chloride (HCl) 1 6/2/2009 8.56E-05 -9.37E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 4 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

Hydrogen Chloride (HCl) 2 6/2/2009 6.85E-05 -9.59E+00 Coal: Bituminous - 100.00 - - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 4 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

Hydrogen Chloride (HCl) 3 6/3/2009 3.13E-05 -1.04E+01 Coal: Bituminous - 100.00 - - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #1 8/18/2009 2.35E-03 -6.05E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #1 11/7/2007 8.95E-05 -9.32E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 68.84 31.16 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #1 11/3/2005 1.20E-03 -6.73E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 40.69 59.31 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #1 11/25/2003 2.90E-04 -8.14E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 57.02 42.98 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main 

Boiler

Hydrogen Chloride (HCl) Sample #2 8/18/2009 2.40E-04 -8.33E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #2 11/7/2007 ND 6.01E-05 -9.72E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 68.84 31.16 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #2 11/25/2003 ND 1.09E-04 -9.12E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 57.02 42.98 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #2 11/3/2005 1.30E-03 -6.65E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 40.69 59.31 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #3 8/19/2009 2.15E-03 -6.14E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride 

(HCl) Sample #3 11/7/2007 ND 5.10E-05 -9.88E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 68.84 31.16 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #3 11/25/2003 ND 1.09E-04 -9.12E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 57.02 42.98 - - 

 

YES Coal 5 SCCogenSouth

B001 - Main Boiler

Hydrogen Chloride (HCl) Sample #3 11/3/2005 1.50E-03 -6.50E+00

/Coal: Bituminous/Industrial Sludge/Wood: Bark/ - 40.69 59.31 - - 

 

YES Coal 6 TNEastman_NO_CBIDATA Boiler 30

Hydrogen Chloride (HCl) Sample #1 8/26/2009 ND 7.30E-05 -9.53E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 6 TNEastman_NO_CBIDATA Boiler 30

Hydrogen Chloride (HCl) Sample #2 8/27/2009 ND 7.30E-05 -9.53E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 6 TNEastman_NO_CBIDATA Boiler 30

Hydrogen Chloride (HCl) Sample #3 8/27/2009 ND 7.10E-05 -9.55E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 7 AZCatalystPaperSnowflake

Power Boiler #2 Coal

Hydrogen Chloride (HCl) Sample #1 3/24/2006 1.83E-04 -8.61E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 7 AZCatalystPaperSnowflake

Power Boiler #2 Coal

Hydrogen Chloride (HCl) Sample #2 3/24/2006 7.69E-05 -9.47E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 7 AZCatalystPaperSnowflake

Power Boiler #2 Coal

Hydrogen Chloride (HCl) Sample #3 3/24/2006 8.86E-05 -9.33E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 8 MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #1 10/4/2006 1.79E-04 -8.63E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 8 MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #1 12/6/2005 8.48E-05 -9.38E+00 /Coal: Sub-bituminous/Natural gas/
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 8 MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #2 10/4/2006 2.27E-04 -8.39E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 8 MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #2 12/6/2005 3.81E-04 -7.87E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 8 MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #3 12/6/2005 3.38E-04 -7.99E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 8 MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #3 10/4/2006 2.30E-04 -8.38E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 9 MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #1 12/6/2005 8.48E-05 -9.38E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 9 MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #1 10/4/2006 1.79E-04 -8.63E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 9 MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #2 10/4/2006 2.27E-04 -8.39E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 9 MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #2 12/6/2005 3.81E-04 -7.87E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 9 MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #3 10/4/2006 2.30E-04 -8.38E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 9 MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #3 12/6/2005 3.38E-04 -7.99E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 10 ALIPCourtland

No.2 Combination Boiler / 11CU201

Hydrogen Chloride (HCl) Sample #1 9/10/1996 3.86E-04 -7.86E+00

/Coal: Bituminous/Natural gas/Noncondensable Gas (includes stripper offgas)/Wood: Bark/

YES Coal 10 ALIPCourtland

No.2 Combination Boiler / 11CU201

Hydrogen Chloride (HCl) Sample #2 9/10/1996 ND 2.55E-04 -8.27E+00

/Coal: Bituminous/Natural gas/Noncondensable Gas (includes stripper offgas)/Wood: Bark/

YES Coal 10 ALIPCourtland

No.2 Combination Boiler / 11CU201

Hydrogen Chloride (HCl) Sample #3 9/10/1996 ND 2.06E-04 -8.49E+00

/Coal: Bituminous/Natural gas/Noncondensable Gas (includes stripper offgas)/Wood: Bark/

YES Coal 11 IDTASCOPaul

Babcock and Wilcox (B&W) Boiler

Hydrogen Chloride (HCl) Sample #1 6/1/2006 ND 3.00E-04 -8.11E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 12 NDMinnDakFarmers

Babcock and Wilcox Boiler #5

Hydrogen Chloride (HCl) Sample #1 10/26/2006 5.14E-04 -7.57E+00 /Biogas/Coal: Sub-bituminous/ - 97.66 - - - 

 

YES Coal 12 NDMinnDakFarmers

Babcock and Wilcox Boiler #5

Hydrogen Chloride (HCl) Sample #2 10/26/2006 2.77E-04 -8.19E+00 /Biogas/Coal: Sub-bituminous/ - 97.66 - - - 

 

YES Coal 12 NDMinnDakFarmers

Babcock and Wilcox Boiler #5

Hydrogen Chloride (HCl) Sample #3 10/26/2006 3.03E-04 -8.10E+00 /Biogas/Coal: Sub-bituminous/ - 97.66 - - - 

 

YES Coal 13

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Hydrogen Chloride (HCl) Sample #1 8/24/2009 ND 3.81E-04 -7.87E+00 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 13

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Hydrogen Chloride (HCl) Sample #2 8/24/2009 ND 3.77E-04 -7.88E+00 Coal: Sub-bituminous - 100.00 - - - 

 

YES Coal 13

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Hydrogen Chloride (HCl) Sample #3 8/25/2009 ND 4.07E-04 -7.81E+00 Coal: Sub-bituminous - 100.00 - - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 14 VAUniversityofVirginia 7103-1-01R

Hydrogen Chloride (HCl) M26A-1 9/15/2009 < 5.80E-04 -7.45E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 14 VAUniversityofVirginia 7103-1-01R

Hydrogen Chloride (HCl) M26A-2 9/16/2009 5.91E-04 -7.43E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 14 VAUniversityofVirginia 7103-1-01R

Hydrogen Chloride (HCl) M26A-3 9/17/2009 < 5.37E-04 -7.53E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 15 WINewPageBiron B24

Hydrogen Chloride (HCl) 1 8/25/2009 2.00E-03 -6.22E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 15 WINewPageBiron B24

Hydrogen Chloride (HCl) 2 9/22/2009 1.95E-03 -6.24E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 15 WINewPageBiron B24

Hydrogen Chloride (HCl) 3 9/22/2009 2.18E-03 -6.13E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

YES Coal 15 WINewPageBiron B24

Hydrogen Chloride (HCl) Sample #1 9/12/2007 5.40E-04 -7.52E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 15 WINewPageBiron B24

Hydrogen Chloride (HCl) Sample #2 9/12/2007 5.20E-04 -7.56E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 15 WINewPageBiron B24

Hydrogen Chloride (HCl) Sample #3 9/12/2007 7.00E-04 -7.26E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 16 MICityofEscanaba

EUBOILER#1

Hydrogen Chloride (HCl) Sample #1 10/27/2004 6.00E-04 -7.42E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 16 MICityofEscanaba

EUBOILER#1

Hydrogen Chloride (HCl) Sample #2 10/27/2004 6.00E-04 -7.42E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 16 MICityofEscanaba

EUBOILER#1

Hydrogen Chloride (HCl) Sample #3 10/27/2004 6.00E-04 -7.42E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #1 9/26/2009 7.40E-04 -7.21E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 17 VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #2 9/26/2009 5.04E-04 -7.59E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 17 VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #3 9/26/2009 7.62E-04 -7.18E+00 Coal: Bituminous - 100.00 - - - 

 

YES Coal 17 VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #1 11/8/2004 8.68E-03 -4.75E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #2 11/8/2004 6.24E-03 -5.08E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 17 VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #3 11/8/2004 7.22E-03 -4.93E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 18 TNEastman_NO_CBIDATA Boiler 31

Hydrogen Chloride (HCl) Sample #1 3/15/2005 ND 7.00E-04 -7.26E+00 /Coal: Bituminous/Process gas/

YES Coal 18 TNEastman_NO_CBIDATA Boiler 31

Hydrogen Chloride (HCl) Sample #2 3/15/2005 ND 7.00E-04 -7.26E+00 /Coal: Bituminous/Process gas/

YES Coal 18 TNEastman_NO_CBIDATA Boiler 31

Hydrogen Chloride (HCl) Sample #3 3/15/2005 ND 7.00E-04 -7.26E+00 /Coal: Bituminous/Process gas/
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 19 WINewPage-WisconsinRapids

Power Boiler 1 - B21

Hydrogen Chloride (HCl) Sample #1 12/14/2005 3.00E-04 -8.11E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 WINewPage-WisconsinRapids

Power Boiler 1 - B21

Hydrogen Chloride (HCl) Sample #2 12/15/2005 1.40E-03 -6.57E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 19 WINewPage-WisconsinRapids

Power Boiler 1 - B21

Hydrogen Chloride (HCl) Sample #3 12/15/2005 7.00E-04 -7.26E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 PADomtarJohnsonburg

#81 Coal Boiler

Hydrogen Chloride (HCl) Sample #1 7/18/2007 8.00E-04 -7.13E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 PADomtarJohnsonburg

#81 Coal Boiler

Hydrogen Chloride (HCl) Sample #2 7/18/2007 1.00E-03 -6.91E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 PADomtarJohnsonburg

#81 Coal Boiler

Hydrogen Chloride 

(HCl) Sample #3 7/17/2007 7.00E-04 -7.26E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 PADomtarJohnsonburg

#82 Coal Boiler

Hydrogen Chloride (HCl) Sample #1 7/18/2007 8.00E-04 -7.13E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 PADomtarJohnsonburg

#82 Coal Boiler

Hydrogen Chloride (HCl) Sample #2 7/18/2007 1.00E-03 -6.91E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 20 PADomtarJohnsonburg

#82 Coal Boiler

Hydrogen Chloride (HCl) Sample #3 7/17/2007 7.00E-04 -7.26E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 22 IDTASCONampa

Babcock and Wilcox (B&W) #1

Hydrogen Chloride (HCl) Sample #1 12/5/2006 9.00E-04 -7.01E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 22 IDTASCONampa

Babcock and Wilcox (B&W) #1

Hydrogen Chloride (HCl) Sample #2 12/5/2006 9.00E-04 -7.01E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 22 IDTASCONampa

Babcock and Wilcox (B&W) #1

Hydrogen Chloride (HCl) Sample #3 12/5/2006 9.00E-04 -7.01E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 22 IDTASCONampa

Babcock and Wilcox (B&W) #2

Hydrogen Chloride 

(HCl) Sample #1 12/5/2006 9.00E-04 -7.01E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 22 IDTASCONampa

Babcock and Wilcox (B&W) #2

Hydrogen Chloride (HCl) Sample #2 12/5/2006 9.00E-04 -7.01E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 22 IDTASCONampa

Babcock and Wilcox (B&W) #2

Hydrogen Chloride (HCl) Sample #3 12/5/2006 9.00E-04 -7.01E+00 /Coal: Sub-bituminous/Natural gas/

YES Coal 22 WINewPage-WisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #1 5/22/2003 9.90E-03 -4.62E+00 /Coal: Sub-bituminous/Wood: Bark/ - 44.51 55.49 - - 

 

YES Coal 22 WINewPage-WisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #1 5/21/2003 8.00E-04 -7.13E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 22 WINewPage-WisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #2 5/22/2003 ND 1.00E-04 -9.21E+00 /Coal: Sub-bituminous/Wood: Bark/ - 44.51 55.49 - - 

 

YES Coal 22 WINewPage-WisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #2 5/21/2003 1.10E-03 -6.81E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 22 WINewPage-WisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride 

(HCl) Sample #3 5/21/2003 8.00E-04 -7.13E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 25 NCBlueRidgePaper G11042

Hydrogen Chloride (HCl) 1 8/4/2009 7.47E-04 -7.20E+00

Coal: Bituminous/Wood: Unadulterated Timber - 65.97 34.03 - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 25 NCBlueRidgePaper G11042

Hydrogen Chloride (HCl) 2 8/4/2009 9.57E-04 -6.95E+00

Coal: Bituminous/Wood: Unadulterated Timber - 65.97 34.03 - - 

 

YES Coal 25 NCBlueRidgePaper G11042

Hydrogen Chloride (HCl) 3 8/5/2009 1.22E-03 -6.71E+00

Coal: Bituminous/Wood: Unadulterated Timber - 65.97 34.03 - - 

 

YES Coal 25 NCBlueRidgePaper G11042

Hydrogen Chloride (HCl) Sample #1 1/12/1994 1.90E-03 -6.27E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 NCBlueRidgePaper G11042

Hydrogen Chloride (HCl) Sample #2 1/12/1994 3.20E-03 -5.74E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 25 NCBlueRidgePaper G11042

Hydrogen Chloride (HCl) Sample #3 1/12/1994 3.30E-03 -5.71E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 26 IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #1 4/22/2004 9.67E-04 -6.94E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 26 IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #1 4/22/2004 5.50E-03 -5.20E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 26 IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #2 4/22/2004 1.16E-03 -6.76E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 26 IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #2 4/22/2004 4.20E-03 -5.47E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 26 IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #3 4/22/2004 1.30E-03 -6.65E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 26 IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #3 4/22/2004 3.70E-03 -5.60E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 27

IDAmalgamatedSugarCoTwinFalls S-B2

Hydrogen Chloride (HCl) Sample #1 9/28/2006 2.00E-03 -6.21E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 27

IDAmalgamatedSugarCoTwinFalls S-B2

Hydrogen Chloride (HCl) Sample #2 9/28/2006 1.00E-03 -6.91E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 27

IDAmalgamatedSugarCoTwinFalls S-B2

Hydrogen Chloride (HCl) Sample #3 9/28/2006 1.00E-03 -6.91E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 27

OHPainesvilleMunicipalElectric B004

Hydrogen Chloride (HCl) Sample #1 8/23/2006 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27

OHPainesvilleMunicipalElectric B004

Hydrogen Chloride (HCl) Sample #2 8/23/2006 1.00E-03 -6.91E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 27

OHPainesvilleMunicipalElectric B004

Hydrogen Chloride (HCl) Sample #3 8/23/2006 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #1 7/13/2006 1.39E-01 -1.97E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #1 2/9/2005 1.46E-03 -6.53E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #2 2/9/2005 1.41E-03 -6.57E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #2 7/13/2006 1.37E-01 -1.99E+00 /Coal: Bituminous/ - 100.00 - - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 29 MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #3 7/13/2006 1.40E-01 -1.97E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 29 MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #3 2/9/2005 1.47E-03 -6.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 30 GAGPCedarSprings

U500 - Power Boiler No 1

Hydrogen Chloride (HCl) 1 7/23/2009 1.82E-03 -6.31E+00

Coal: Bituminous/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - 58.66 34.21 - - 

 

YES Coal 30 GAGPCedarSprings

U500 - Power Boiler No 1

Hydrogen Chloride (HCl) 2 7/23/2009 1.66E-03 -6.40E+00

Coal: Bituminous/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - 58.66 34.21 - - 

 

YES Coal 30 GAGPCedarSprings

U500 - Power Boiler No 1

Hydrogen Chloride (HCl) 3 7/24/2009 1.18E-03 -6.74E+00

Coal: Bituminous/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - 58.66 34.21 - - 

 

YES Coal 31 WYGeneralChemical

GR-2-L (C BOILER)

Hydrogen Chloride (HCl) Sample #1 10/27/2004 1.70E-03 -6.38E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 31 WYGeneralChemical

GR-2-L (C BOILER)

Hydrogen Chloride (HCl) Sample #2 10/27/2004 1.70E-03 -6.38E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 31 WYGeneralChemical

GR-2-L (C BOILER)

Hydrogen Chloride (HCl) Sample #3 10/27/2004 2.00E-03 -6.21E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 32 TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #1 3/10/2005 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #1 3/9/2005 1.60E-03 -6.44E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #2 3/10/2005 3.20E-03 -5.74E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #2 3/9/2005 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #3 3/9/2005 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 32 TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #3 3/10/2005 8.30E-03 -4.79E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPrairiePowerPearl B1

Hydrogen Chloride (HCl) Sample #1 5/4/2005 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPrairiePowerPearl B1

Hydrogen Chloride (HCl) Sample #2 5/4/2005 1.90E-03 -6.27E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 33 ILPrairiePowerPearl B1

Hydrogen Chloride (HCl) Sample #3 5/4/2005 1.90E-03 -6.27E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 34 WYGeneralChemical

GR-3-W (D BOILER)

Hydrogen Chloride (HCl) Sample #1 10/21/2004 2.00E-03 -6.21E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 34 WYGeneralChemical

GR-3-W (D BOILER)

Hydrogen Chloride (HCl) Sample #2 10/21/2004 2.00E-03 -6.21E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 34 WYGeneralChemical

GR-3-W (D BOILER)

Hydrogen Chloride (HCl) Sample #3 10/21/2004 1.90E-03 -6.27E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 35 MNAmericanCrystalMoorhead Boiler 3

Hydrogen Chloride (HCl) Sample #1 11/16/2004 8.93E-04 -7.02E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 35 MNAmericanCrystalMoorhead Boiler 3

Hydrogen Chloride (HCl) Sample #2 11/16/2004 2.89E-03 -5.85E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 35 MNAmericanCrystalMoorhead Boiler 3

Hydrogen Chloride (HCl) Sample #3 11/16/2004 2.20E-03 -6.12E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

 

YES Coal 36

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #1 5/28/2004 4.00E-03 -5.52E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #1 8/4/2006 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #2 8/4/2006 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #2 5/28/2004 1.20E-02 -4.42E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #3 8/4/2006 2.00E-03 -6.21E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 36

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #3 5/28/2004 6.00E-03 -5.12E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #1 4/6/2005 3.17E-03 -5.75E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #1 6/27/2006 3.30E-03 -5.71E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #2 4/6/2005 1.75E-03 -6.35E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Erie 

Boiler

Hydrogen Chloride (HCl) Sample #2 6/27/2006 5.50E-03 -5.20E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #3 4/6/2005 3.05E-03 -5.79E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #3 6/27/2006 5.90E-03 -5.13E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #1 6/27/2006 3.30E-03 -5.71E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #1 4/7/2005 3.17E-03 -5.75E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #2 6/27/2006 5.50E-03 -5.20E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #2 4/7/2005 1.75E-03 -6.35E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #3 6/27/2006 5.90E-03 -5.13E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 37 INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #3 4/7/2005 3.05E-03 -5.79E+00 /Coal: Bituminous/ - 100.00 - - - 

 

YES Coal 39 WINewPage-Whiting B24

Hydrogen Chloride (HCl) Sample #1 8/24/2006 2.00E-03 -6.21E+00 /Coal: Bituminous/Wood: Bark/ - 66.09 33.91 - - 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal 39 WINewPage-Whiting B24

Hydrogen Chloride (HCl) Sample #2 8/24/2006 3.30E-03 -5.71E+00 /Coal: Bituminous/Wood: Bark/ - 66.09 33.91 - - 

 

YES Coal 39 WINewPage-Whiting B24

Hydrogen Chloride (HCl) Sample #3 8/24/2006 2.90E-03 -5.84E+00 /Coal: Bituminous/Wood: Bark/ - 66.09 33.91 - - 

 

YES Gas 1 1 SCMichelinSandySprings B:02:01

Hydrogen Chloride (HCl) Sample #1 9/10/2009 1.14E-04 -9.08E+00 Natural gas - - - - - 

 

YES Gas 1 1 SCMichelinSandySprings B:02:01

Hydrogen Chloride (HCl) Sample #2 9/10/2009 ND 3.84E-05 -1.02E+01 Natural gas - - - - - 

 

YES Gas 1 1 SCMichelinSandySprings B:02:01

Hydrogen Chloride (HCl) Sample #3 9/10/2009 ND 6.56E-05 -9.63E+00 Natural gas - - - - - 

 

YES Gas 1 2 WYSinclairWyoming

Pt 74 #2 H2 Plant Heater

Hydrogen Chloride (HCl) 1 11/18/2009 DL 1.26E-04 -8.98E+00 Natural gas - - - - - 

 

YES Gas 1 2 WYSinclairWyoming

Pt 74 #2 H2 Plant Heater

Hydrogen Chloride (HCl) 2 11/18/2009 DL 1.30E-04 -8.95E+00 Natural gas - - - - - 

 

YES Gas 1 2 WYSinclairWyoming

Pt 74 #2 H2 Plant Heater

Hydrogen Chloride (HCl) 3 11/18/2009 DL 1.30E-04 -8.95E+00 Natural gas - - - - - 

 

YES Gas 1 y 1 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088

Hydrogen Chloride (HCl) M26-1 8/13/2009 9.81E-05 -9.23E+00 Natural gas - - - - - 

 

YES Gas 1 y 1 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088

Hydrogen Chloride (HCl) M26-2 8/14/2009 8.39E-05 -9.39E+00 Natural gas - - - - - 

 

YES Gas 1 y 1 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088

Hydrogen Chloride (HCl) M26-3 8/14/2009 7.58E-05 -9.49E+00 Natural gas - - - - - 

 

YES Gas 1 y 2 INAlcoaWarrick

Annealing 

Furnace #15

Hydrogen Chloride (HCl) M26A-1 8/17/2009 BDL 2.54E-04 -8.28E+00 /Natural gas/

YES Gas 1 y 2 INAlcoaWarrick

Annealing Furnace #15

Hydrogen Chloride (HCl) M26A-2 8/17/2009 BDL 2.34E-04 -8.36E+00 /Natural gas/

YES Gas 1 y 2 INAlcoaWarrick

Annealing Furnace #15

Hydrogen Chloride (HCl) M26A-3 8/17/2009 BDL 2.48E-04 -8.30E+00 /Natural gas/

YES Gas 1 y 2 INAlcoaWarrick

Pre-Heat Furnace #36

Hydrogen Chloride (HCl) M26A-1 8/17/2009 BDL 2.54E-04 -8.28E+00 Natural gas - - - - - 

 

YES Gas 1 y 2 INAlcoaWarrick

Pre-Heat Furnace #36

Hydrogen Chloride (HCl) M26A-2 8/17/2009 BDL 2.34E-04 -8.36E+00 Natural gas - - - - - 

 

YES Gas 1 y 2 INAlcoaWarrick

Pre-Heat Furnace #36

Hydrogen Chloride (HCl) M26A-3 8/17/2009 BDL 2.48E-04 -8.30E+00 Natural gas - - - - - 

 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801

Hydrogen Chloride (HCl) Sample #1 8/25/2009 ND 1.57E-06 -1.34E+01

Heavy Recycle/Natural gas/Petrochemical process gas - - - - - 

 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801

Hydrogen Chloride (HCl) Sample #2 8/26/2009 ND 1.85E-06 -1.32E+01

Heavy Recycle/Natural gas/Petrochemical process gas - - - - - 

 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801

Hydrogen Chloride (HCl) Sample #3 8/27/2009 ND 1.68E-06 -1.33E+01

Heavy Recycle/Natural gas/Petrochemical process gas - - - - - 

 

YES Liquid 3 SCMilliken-Dewey D30

Hydrogen Chloride (HCl) Sample #1 8/13/2009 ND 1.00E-04 -9.21E+00 Anhydrides Waste - - - - 100.00 

 
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid 3 SCMilliken-Dewey D30

Hydrogen Chloride (HCl) Sample #2 8/13/2009 ND 1.00E-04 -9.21E+00 Anhydrides Waste - - - - 100.00 

 

YES Liquid 3 SCMilliken-Dewey D30

Hydrogen Chloride (HCl) Sample #3 8/13/2009 ND 1.00E-04 -9.21E+00 Anhydrides Waste - - - - 100.00 

 

YES Liquid 4 TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #1 8/31/2006 1.95E-04 -8.54E+00 /No. 2 Distillate/ - - - - - 

 

YES Liquid 4 TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #1 7/29/2009 ND 6.18E-04 -7.39E+00 No. 2 Distillate - - - - - 

 

YES Liquid 4 TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #2 8/31/2006 2.09E-04 -8.47E+00 /No. 2 Distillate/ - - - - - 

 

YES Liquid 4 TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #2 7/30/2009 ND 6.19E-04 -7.39E+00 No. 2 Distillate - - - - - 

 

YES Liquid 4 TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #3 8/31/2006 1.28E-04 -8.96E+00 /No. 2 Distillate/ - - - - - 

 

YES Liquid 4 TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #3 7/30/2009 ND 6.24E-04 -7.38E+00 No. 2 Distillate - - - - - 

 

YES Liquid 5 INUSSteelGaryWorks O4B10459

Hydrogen Chloride (HCl) M26A-1 9/8/2009 2.33E-04 -8.36E+00

Blast Furnace Gas/Natural gas/No. 6 Residual oil - - - - 13.43 

 

YES Liquid 5 INUSSteelGaryWorks O4B10459

Hydrogen Chloride (HCl) M26A-2 9/8/2009 1.88E-04 -8.58E+00

Blast Furnace Gas/Natural gas/No. 6 Residual oil - - - - 13.43 

 

YES Liquid 5 INUSSteelGaryWorks O4B10459

Hydrogen Chloride (HCl) M26A-3 9/8/2009 1.99E-04 -8.52E+00

Blast Furnace Gas/Natural gas/No. 6 Residual oil - - - - 13.43 

 

YES Liquid 6 VAINVISTAWaynesboro

2-205 (V#1) Vaporizer #1

Hydrogen Chloride (HCl) Sample #1 4/18/2008 3.15E-04 -8.06E+00 /No. 6 Residual oil/ - - - - 100.00 

 

YES Liquid 6 VAINVISTAWaynesboro

2-205 (V#1) Vaporizer #1

Hydrogen Chloride (HCl) Sample #2 4/18/2008 2.07E-04 -8.48E+00 /No. 6 Residual oil/ - - - - 100.00 

 

YES Liquid 6 VAINVISTAWaynesboro

2-205 (V#1) Vaporizer #1

Hydrogen Chloride (HCl) Sample #3 4/18/2008 2.08E-04 -8.48E+00 /No. 6 Residual oil/ - - - - 100.00 

 

YES Liquid CTElectric Boat EMU 18 Chlorine (Cl) Sample #1 ND 5.60E-07 -1.44E+01 No. 4 Fuel oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #1 4.40E-06 -1.23E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #10 4.45E-06 -1.23E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #11 4.59E-06 -1.23E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #12 1.02E-05 -1.15E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #2 4.44E-06 -1.23E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #3 6.94E-06 -1.19E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #4 4.14E-06 -1.24E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #5 2.05E-06 -1.31E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #6 3.26E-06 -1.26E+01

Animal Fat/Oils/Tallow/Vegetable Oil
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #7 4.30E-06 -1.24E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #8 4.82E-06 -1.22E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid ILCognisCorp Boiler #2 Chlorine (Cl) Sample #9 3.29E-06 -1.26E+01

Animal Fat/Oils/Tallow/Vegetable Oil

YES Liquid NCCampLejeuneMCB

A-BM-5400-80 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-80 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-80 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-80 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-80 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-80 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-81 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-81 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-81 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-81 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-81 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-5400-81 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-12 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-12 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-12 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-12 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-12 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-12 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-13 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-13 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-13 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-13 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-13 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-825-13 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-825-H1 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-825-H1 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-825-H1 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-825-H1 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-825-H1 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

A-BM-825-H1 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-06 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-06 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-06 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-06 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-06 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-06 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-07 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-07 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-07 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-07 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-07 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-835-07 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-14 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-14 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-14 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-14 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-14 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-14 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-15 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-15 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-15 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-15 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-15 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-BM-890-15 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H10 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H10 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H10 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H10 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H10 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H10 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H9 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

A-BM-890-H9 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H9 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H9 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H9 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-BM-890-H9 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-260-90 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-260-90 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-260-90 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-260-90 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-260-90 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-260-90 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-440-87 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-440-87 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-440-87 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-440-87 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-440-87 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-440-87 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-989-31 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-989-31 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-989-31 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-989-31 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-989-31 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-FC-989-31 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-1700-05 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-1700-05 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-1700-05 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-1700-05 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-1700-05 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-1700-05 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-20 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-20 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-20 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

A-HP-2027-20 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-20 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-20 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-21 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-21 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-21 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-21 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-21 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-21 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H13 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H13 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H13 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H13 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H13 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H13 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H14 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H14 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H14 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H14 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H14 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H14 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H15 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H15 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H15 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H15 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H15 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H15 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H16 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H16 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H16 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H16 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-HP-2027-H16 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

A-HP-2027-H16 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-75 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-75 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-75 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-75 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-75 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-75 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-76 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-76 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-76 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-76 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-76 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-40-76 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-500-86 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-500-86 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-500-86 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-500-86 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-500-86 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-500-86 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-670-88 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-670-88 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-670-88 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-670-88 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-670-88 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-670-88 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-HP-989-31 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB A-HP-989-31 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-989-31 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-989-31 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-989-31 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-HP-989-31 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4014-17 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4014-17 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4014-17 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4014-17 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4014-17 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4014-17 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-MG-SH8-

58 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-121-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB A-NH-121-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-121-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-121-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-121-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-NH-121-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-

H7 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-10 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-10 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-10 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

A-PP-2615-10 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-10 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-PP-2615-10 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-TT-2457-66 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-TT-2457-66 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-TT-2457-66 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-TT-2457-66 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-TT-2457-66 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

A-TT-2457-66 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-44-30 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-44-30 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-44-30 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-44-30 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-44-30 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-44-30 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-78 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-78 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-78 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-78 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-78 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-78 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB A-TT-60-79 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-TT-60-79 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-TT-60-79 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-TT-60-79 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-TT-60-79 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB A-TT-60-79 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB B-A66-48 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB B-A66-48 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB B-A66-48 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB B-A66-48 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB B-A66-48 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB B-A66-48 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A66-H3 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A66-H3 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A66-H3 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A66-H3 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A66-H3 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A66-H3 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-49 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-49 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-49 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-49 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-49 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-49 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-H5 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-H5 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-H5 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-H5 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-H5 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A71-H5 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A1-50 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A1-50 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A1-50 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A1-50 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A1-50 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A1-50 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A47-51 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A47-51 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A47-51 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A47-51 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A47-51 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-A-A47-51 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-49-52 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB B-BB-49-52 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-49-52 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-49-52 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-49-52 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-49-52 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-53B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-53B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-53B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-53B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-53B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-53B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-54 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-54 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-54 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-54 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-54 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-54 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-55 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-55 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-55 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-55 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-55 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB B-BB-9-55 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-20 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-

20 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-20 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-20 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-20 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-20 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-H21 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-H21 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-H21 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

C-AS-1000-H21 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-H21 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-1000-H21 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-2800-12 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-2800-12 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-2800-12 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-2800-12 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-2800-12 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-2800-12 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3502-08 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3502-08 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3502-08 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3502-08 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3502-08 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3502-08 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3504-09 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3504-09 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3504-09 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3504-09 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3504-09 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3504-09 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3525-15 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3525-15 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3525-15 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3525-15 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3525-15 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-3525-15 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-22 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-22 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-22 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-22 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-22 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

C-AS-4044-22 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-23 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-23 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-23 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-23 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-23 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4044-23 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-17A Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-17A Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-17A Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-17A Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-17A Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-17A Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-18 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-18 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-18 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-18 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-18 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-AS-4151-18 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-705-11 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-705-11 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-705-11 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-705-11 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-705-11 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-705-11 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-710-03 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-710-03 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-710-03 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-710-03 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-710-03 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-710-03 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation FuelYES Liquid NCCampLejeuneMCB C-AS-840-13 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB C-AS-840-13 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-840-13 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-840-13 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-840-13 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-840-13 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-843-14 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-843-14 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-843-14 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-843-14 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-843-14 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB C-AS-843-14 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-480-89 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-480-89 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-480-89 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-480-89 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-480-89 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-480-89 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-83B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-83B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-83B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-

83B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-83B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-83B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-84B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-84B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-84B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-84B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-84B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-84B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-85 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-85 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-85 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

C-CG-650-85 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-85 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-CG-650-85 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-RR-15-46B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-RR-15-46B Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-RR-15-46B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-RR-15-46B Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-RR-15-46B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-RR-15-46B Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-TC-1500-60 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-TC-1500-60 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-TC-1500-60 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-TC-1500-60 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-TC-1500-60 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-TC-1500-60 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM103-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM103-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM103-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM103-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM103-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM103-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM104-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM104-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM104-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM104-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM104-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM104-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-6: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect? lb/mmBtu

ln 

(lb/mmBtu) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid NCCampLejeuneMCB

C-VLTFM203-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-02 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-02 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-02 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-02 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-02 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM203-02 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-01 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-01 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-01 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-02 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-02 Chlorine (Cl) Sample #1 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-02 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-02 Chlorine (Cl) Sample #2 ND 2.65E-04 -8.24E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-02 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel

YES Liquid NCCampLejeuneMCB

C-VLTFM204-02 Chlorine (Cl) Sample #3 ND 2.65E-04 -8.23E+00 No. 2 Distillate/JP-8 Aviation Fuel
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 1 OKVRCOklahoma H-101 CO Sample #3 10/22/1998 9.36E-03 -4.67E+00 /Refinery gas/ - - - - - 

YES Gas 1 2 OKVRCOklahoma H-102A CO Sample #1 10/20/1998 3.46E-01 -1.06E+00 /Refinery gas/ - - - - - YES Gas 1 2 OKVRCOklahoma H-102A CO Sample #1 10/21/1998 1.01E-02 -4.59E+00 /Refinery gas/ - - - - - YES Gas 1 2 OKVRCOklahoma H-102A CO Sample #2 12/3/1997 1.74E-01 -1.75E+00 /Refinery gas/ - - - - - YES Gas 1 2 OKVRCOklahoma H-102A CO Sample #2 12/3/1997 1.04E-01 -2.27E+00 /Refinery gas/ - - - - - YES Gas 1 2 OKVRCOklahoma H-102A CO Sample #2 10/20/1998 9.43E+00 2.24E+00 /Refinery gas/ - - - - - YES Gas 1 2 OKVRCOklahoma H-102A CO Sample #3 10/20/1998 2.04E+01 3.02E+00 /Refinery gas/ - - - - - YES Gas 1 3 TXRohmHaasDeerPark ACET-2B-4 CO Sample #1 11/29/2006 ND 1.00E-02 -4.61E+00 /Refinery gas/ - - - - - YES Gas 1 3 TXRohmHaasDeerPark ACET-2B-4 CO Sample #1 11/30/2006 1.96E+00 6.73E-01 /Natural gas/ - - - - - 

YES Gas 1 3 TXRohmHaasDeerPark ACET-2B-4 CO Sample #2 11/30/2006 4.16E+00 1.43E+00 /Natural gas/ - - - - - YES Gas 1 3 TXRohmHaasDeerPark ACET-2B-4 CO Sample #2 11/29/2006 ND 2.00E-02 -3.91E+00 /Refinery gas/ - - - - - 

YES Gas 1 3 TXRohmHaasDeerPark ACET-2B-4 CO Sample #3 11/30/2006 4.91E+00 1.59E+00 /Natural gas/ - - - - - 

YES Gas 1 3 TXRohmHaasDeerPark ACET-2B-4 CO Sample #3 11/29/2006 ND 1.00E-02 -4.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #1 7/7/2006 6.40E-01 -4.46E-01 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #1 10/5/2006 3.00E-01 -1.20E+00 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #1 5/9/2007 1.16E+00 1.48E-01 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #1 6/4/2008 1.19E+01 2.48E+00 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #2 5/24/2006 4.00E-02 -3.22E+00 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #2 10/5/2006 1.56E+00 4.45E-01 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #2 5/9/2007 9.60E-01 -4.08E-02 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #2 5/11/2006 1.00E-02 -4.61E+00 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #3 5/11/2006 3.00E-02 -3.51E+00 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #3 5/24/2006 2.24E+00 8.06E-01 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #3 10/5/2006 2.57E+00 9.44E-01 /Refinery gas/ - - - - - YES Gas 1 4 OKConocoPhillipsPoncaCity H-9902 CO Sample #3 5/9/2007 1.23E+00 2.07E-01 /Refinery gas/ - - - - - YES Gas 1 5

TXDiamondShamrockThreeRivers H-201 CO Sample #1 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 5

TXDiamondShamrockThreeRivers H-201 CO Sample #2 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 5

TXDiamondShamrockThreeRivers H-201 CO Sample #3 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 6

TXDiamondShamrockThreeRivers H-203 CO Sample #1 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 6

TXDiamondShamrockThreeRivers H-203 CO Sample #2 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 6

TXDiamondShamrockThreeRivers H-203 CO Sample #3 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 7

TXDiamondShamrockThreeRivers H-204 CO Sample #1 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 7

TXDiamondShamrockThreeRivers H-204 CO Sample #2 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 7

TXDiamondShamrockThreeRivers H-204 CO Sample #3 7/3/1997 2.71E-02 -3.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 8 VAWesternRefiningYorktown F-562 CO Sample #1 3/7/2007 3.94E-02 -3.23E+00 /Refinery gas/ - - - - - 

YES Gas 1 9 OKConocoPhillipsPoncaCity H-9851 CO Sample #1 6/5/2008 4.00E-02 -3.22E+00 /Process gas/Refinery gas/ - - - - - 

YES Gas 1 9 OKConocoPhillipsPoncaCity H-9851 CO Sample #1 5/4/2006 5.00E-02 -3.00E+00 /Process gas/Refinery gas/ - - - - - YES Gas 1 9 OKConocoPhillipsPoncaCity H-9851 CO Sample #2 5/4/2006 1.10E-01 -2.21E+00 /Process gas/Refinery gas/ - - - - - YES Gas 1 9 OKConocoPhillipsPoncaCity H-9851 CO Sample #3 5/4/2006 1.00E-01 -2.30E+00 /Process gas/Refinery gas/ - - - - - YES Gas 1 10 INBPWhitingRefinery B-601 CO Sample #1 8/20/2007 1.10E-01 -2.21E+00 /Natural gas/ - - - - - 

YES Gas 1 10 INBPWhitingRefinery B-601 CO Sample #2 8/20/2007 ND 1.00E-02 -4.61E+00 /Natural gas/ - - - - - YES Gas 1 10 INBPWhitingRefinery B-601 CO Sample #3 8/20/2007 ND 1.00E-02 -4.61E+00 /Natural gas/ - - - - - YES Gas 1 11 OKConocoPhillipsPoncaCity H-0016 CO Sample #1 4/6/2005 6.00E-02 -2.81E+00 /Refinery gas/ - - - - - 

YES Gas 1 11 OKConocoPhillipsPoncaCity H-0016 CO Sample #2 4/6/2005 2.00E-02 -3.91E+00 /Refinery gas/ - - - - - YES Gas 1 11 OKConocoPhillipsPoncaCity H-0016 CO Sample #3 4/6/2005 5.00E-02 -3.00E+00 /Refinery gas/ - - - - - YES Gas 1 12 TXOccidentalChemGregory

VCM Plant 1 Furnace 1 CO Sample #1 3/5/1991 ND 5.06E-02 -2.98E+00 /Natural gas/ - - - - - 

YES Gas 1 12 TXOccidentalChemGregory

VCM Plant 1 Furnace 1 CO Sample #2 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 12 TXOccidentalChemGregory

VCM Plant 1 Furnace 1 CO Sample #3 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 13 TXOccidentalChemGregory

VCM Plant 1 Furnace 2 CO Sample #1 3/5/1991 ND 5.06E-02 -2.98E+00 /Natural gas/ - - - - - 

YES Gas 1 13 TXOccidentalChemGregory

VCM Plant 1 Furnace 2 CO Sample #2 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 13 TXOccidentalChemGregory

VCM Plant 1 Furnace 2 CO Sample #3 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 14 TXOccidentalChemGregory

VCM Plant 1 Furnace 3 CO Sample #1 3/5/1991 ND 5.06E-02 -2.98E+00 /Natural gas/ - - - - - 

YES Gas 1 14 TXOccidentalChemGregory

VCM Plant 1 Furnace 3 CO Sample #2 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 14 TXOccidentalChemGregory

VCM Plant 1 Furnace 3 CO Sample #3 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 15 TXOccidentalChemGregory

VCM Plant 1 Furnace 4 CO Sample #1 3/5/1991 ND 5.06E-02 -2.98E+00 /Natural gas/ - - - - - 

YES Gas 1 15 TXOccidentalChemGregory

VCM Plant 1 Furnace 4 CO Sample #2 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 15 TXOccidentalChemGregory

VCM Plant 1 Furnace 4 CO Sample #3 3/5/1991 ND 5.00E-02 -3.00E+00 /Natural gas/ - - - - - 

YES Gas 1 16 MSChevronPascagoula F-2103 CO Sample #1 3/27/2008 5.41E-02 -2.92E+00 /Refinery gas/ - - - - - 

YES Gas 1 16 MSChevronPascagoula F-2103 CO Sample #2 3/27/2008 5.41E-02 -2.92E+00 /Refinery gas/ - - - - - YES Gas 1 16 MSChevronPascagoula F-2103 CO Sample #3 3/27/2008 5.41E-02 -2.92E+00 /Refinery gas/ - - - - - YES Gas 1 17

TXDiamondShamrockThreeRivers H-1102 CO Sample #1 7/9/1997 6.77E-02 -2.69E+00 /Refinery gas/ - - - - - 

YES Gas 1 17

TXDiamondShamrockThreeRivers H-1102 CO Sample #2 7/9/1997 6.77E-02 -2.69E+00 /Refinery gas/ - - - - - 

YES Gas 1 17

TXDiamondShamrockThreeRivers H-1102 CO Sample #3 7/9/1997 5.41E-02 -2.92E+00 /Refinery gas/ - - - - - 

YES Gas 1 18 NJSunocoWestville Boiler #8 CO Sample #1 10/15/2007 7.89E-02 -2.54E+00 /Refinery gas/ - - - - - 

YES Gas 1 18 NJSunocoWestville Boiler #8 CO Sample #2 10/15/2007 7.89E-02 -2.54E+00 /Refinery gas/ - - - - - YES Gas 1 18 NJSunocoWestville Boiler #8 CO Sample #3 10/15/2007 3.95E-02 -3.23E+00 /Refinery gas/ - - - - - YES Gas 1 19 ILAkzoNobelMorris

B-1 Nebraska Boiler CO Sample #1 3/20/2002 5.87E-02 -2.84E+00 /Natural gas/Nitrile Pitch Residue/ - - - - - 

YES Gas 1 19 ILAkzoNobelMorris

B-1 Nebraska Boiler CO Sample #1 7/28/2009 1.34E+00 2.91E-01 /Natural gas/Nitrile Pitch Residue/ - - - - - 

YES Gas 1 19 ILAkzoNobelMorris

B-1 Nebraska Boiler CO Sample #2 3/20/2002 4.24E-02 -3.16E+00 /Natural gas/Nitrile Pitch Residue/ - - - - - 

YES Gas 1 19 ILAkzoNobelMorris

B-1 Nebraska Boiler CO Sample #2 7/28/2009 8.18E-01 -2.00E-01 /Natural gas/Nitrile Pitch Residue/ - - - - - 

YES Gas 1 19 ILAkzoNobelMorris

B-1 Nebraska Boiler CO Sample #3 3/20/2002 1.19E-01 -2.13E+00 /Natural gas/Nitrile Pitch Residue/ - - - - - 

YES Gas 1 19 ILAkzoNobelMorris

B-1 Nebraska Boiler CO Sample #3 7/29/2009 1.23E-01 -2.10E+00 /Natural gas/Nitrile Pitch Residue/ - - - - - 

YES Gas 1 20 KYCatlettsburgRefining 2-23-B-4 CO Sample #1 8/12/2005 ND 7.72E-02 -2.56E+00 /Refinery gas/ - - - - - YES Gas 1 20 KYCatlettsburgRefining 2-23-B-4 CO Sample #1 4/21/2004 4.12E-01 -8.87E-01 /Refinery gas/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 20 KYCatlettsburgRefining 2-23-B-4 CO Sample #2 8/12/2005 ND 7.77E-02 -2.55E+00 /Refinery gas/ - - - - - 

YES Gas 1 20 KYCatlettsburgRefining 2-23-B-4 CO Sample #3 8/12/2005 ND 7.75E-02 -2.56E+00 /Refinery gas/ - - - - - YES Gas 1 21 ILWoodRiverRefinery

HTR-DU1-F302 CO Sample #1 4/11/2006 7.88E-02 -2.54E+00 /Refinery gas/ - - - - - 

YES Gas 1 22 PASunocoMarcusHook

705 (12-4 LSG Heater, H01) CO Sample #1 2/4/2008 8.00E-02 -2.53E+00 /Refinery gas/ - - - - - 

YES Gas 1 23 OKVRCOklahoma H-201 CO Sample #1 6/22/2005 7.77E-02 -2.55E+00 /Refinery gas/ - - - - - 

YES Gas 1 23 OKVRCOklahoma H-201 CO Sample #1 6/22/2005 1.84E+02 5.21E+00 /Refinery gas/ - - - - - YES Gas 1 23 OKVRCOklahoma H-201 CO Sample #2 6/22/2005 9.15E-02 -2.39E+00 /Refinery gas/ - - - - - YES Gas 1 23 OKVRCOklahoma H-201 CO Sample #2 6/22/2005 5.56E+01 4.02E+00 /Refinery gas/ - - - - - YES Gas 1 23 OKVRCOklahoma H-201 CO Sample #3 6/22/2005 9.04E-02 -2.40E+00 /Refinery gas/ - - - - - YES Gas 1 24 LACitgoLakeCharles EQT242 CO Sample #1 6/12/2003 8.95E-02 -2.41E+00 /Refinery gas/ - - - - - YES Gas 1 25 MSChevronPascagoula F-6701 CO Sample #1 2/27/2007 1.21E-01 -2.12E+00 /Refinery gas/ - - - - - YES Gas 1 25 MSChevronPascagoula F-6701 CO Sample #2 2/27/2007 8.06E-02 -2.52E+00 /Refinery gas/ - - - - - YES Gas 1 25 MSChevronPascagoula F-6701 CO Sample #3 2/27/2007 7.95E-02 -2.53E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #1 6/13/2006 ND 1.12E-01 -2.19E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #1 6/12/2007 ND 1.06E-01 -2.25E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #1 6/9/2008 ND 9.83E-02 -2.32E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #2 6/13/2006 ND 1.13E-01 -2.18E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #2 6/12/2007 ND 1.07E-01 -2.24E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #2 6/9/2008 ND 9.92E-02 -2.31E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #3 6/13/2006 ND 1.12E-01 -2.19E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #3 6/12/2007 ND 1.08E-01 -2.22E+00 /Refinery gas/ - - - - - YES Gas 1 26 KYCatlettsburgRefining 2-122-B-1 CO Sample #3 6/9/2008 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 27 ALHuntRefining HS-2041A CO Sample #1 6/17/2008 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 28 ALHuntRefining HS-2041B CO Sample #1 6/17/2008 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 29 ALHuntRefining HS-2041C CO Sample #1 6/17/2008 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 30 OKConocoPhillipsPoncaCity H-0003 CO Sample #1 4/12/2002 1.60E-01 -1.83E+00 /Refinery gas/ - - - - - YES Gas 1 30 OKConocoPhillipsPoncaCity H-0003 CO Sample #2 4/12/2002 4.00E-02 -3.22E+00 /Refinery gas/ - - - - - YES Gas 1 31 TXAirProductsBaytown

BOILER (EPN 7) CO Sample #1 1/19/2006 1.00E-01 -2.30E+00 /Hydrogen/CO2/Natural gas/ - - - - - 

YES Gas 1 31 TXAirProductsBaytown

BOILER (EPN 7) CO Sample #2 1/19/2006 1.00E-01 -2.30E+00 /Hydrogen/CO2/Natural gas/ - - - - - 

YES Gas 1 31 TXAirProductsBaytown

BOILER (EPN 7) CO Sample #3 1/19/2006 ND 1.00E-01 -2.30E+00 /Hydrogen/CO2/Natural gas/ - - - - - 

YES Gas 1 32 TXChevronBaytown H-1001 CO Sample #1 6/4/2004 ND 1.00E-01 -2.30E+00 /Natural gas/ - - - - - 

YES Gas 1 32 TXChevronBaytown H-1001 CO Sample #2 6/4/2004 ND 1.00E-01 -2.30E+00 /Natural gas/ - - - - - YES Gas 1 32 TXChevronBaytown H-1001 CO Sample #3 6/4/2004 ND 1.00E-01 -2.30E+00 /Natural gas/ - - - - - YES Gas 1 33 TXEquistarPasadena Boiler (P-25) CO Sample #1 12/6/2007 ND 1.00E-01 -2.30E+00 /Natural gas/Process gas/ - - - - - 

YES Gas 1 33 TXEquistarPasadena Boiler (P-25) CO Sample #2 12/6/2007 ND 1.00E-01 -2.30E+00 /Natural gas/Process gas/ - - - - - 

YES Gas 1 33 TXEquistarPasadena Boiler (P-25) CO Sample #3 12/6/2007 ND 1.00E-01 -2.30E+00 /Natural gas/Process gas/ - - - - - 

YES Gas 1 34 TXValeroTexasCity

Heater 13-1451 CO Sample #1 8/15/2000 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 

YES Gas 1 34 TXValeroTexasCity

Heater 13-1451 CO Sample #2 8/15/2000 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 

YES Gas 1 34 TXValeroTexasCity

Heater 13-1451 CO Sample #3 8/15/2000 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 

YES Gas 1 35 TXValeroTexasCity Heater 16 CO Sample #1 11/1/1999 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 

YES Gas 1 35 TXValeroTexasCity Heater 16 CO Sample #2 11/1/1999 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 35 TXValeroTexasCity Heater 16 CO Sample #3 11/1/1999 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 36 TXValeroTexasCity Heater 17 CO Sample #1 11/1/1999 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 36 TXValeroTexasCity Heater 17 CO Sample #2 11/1/1999 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 36 TXValeroTexasCity Heater 17 CO Sample #3 11/1/1999 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 37 TXValeroTexasCity Heater 28 CO Sample #1 10/31/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 37 TXValeroTexasCity Heater 28 CO Sample #2 10/31/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 37 TXValeroTexasCity Heater 28 CO Sample #3 10/31/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 38 TXValeroTexasCity Heater 35 CO Sample #1 3/14/2007 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 38 TXValeroTexasCity Heater 35 CO Sample #2 3/14/2007 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 

YES Gas 1 38 TXValeroTexasCity Heater 35 CO Sample #3 3/14/2007 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 39 TXValeroTexasCity Heater 44 CO Sample #1 1/6/2000 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 39 TXValeroTexasCity Heater 44 CO Sample #2 1/6/2000 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 39 TXValeroTexasCity Heater 44 CO Sample #3 1/6/2000 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 40 LAWestlakeStyrene 1-90 CO Sample #1 11/10/1992 ND 1.01E-01 -2.29E+00 /Natural gas/ - - - - - 

YES Gas 1 40 LAWestlakeStyrene 1-90 CO Sample #2 11/10/1992 ND 1.02E-01 -2.29E+00 /Natural gas/ - - - - - YES Gas 1 40 LAWestlakeStyrene 1-90 CO Sample #3 11/10/1992 1.00E-01 -2.30E+00 /Natural gas/ - - - - - YES Gas 1 41 OREvrazOregonSteel

EU-5 Vacuum Degasser Boiler CO Sample #3 4/25/2003 1.02E-01 -2.29E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #1 9/12/2000 ND 1.02E-01 -2.28E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #1 9/13/2000 ND 1.35E-01 -2.00E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #1 9/12/2000 ND 1.02E-01 -2.28E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #2 9/13/2000 ND 9.30E-02 -2.38E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol 

Charge Heater) CO Sample #2 9/12/2000 ND 1.02E-01 -2.28E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #3 9/12/2000 ND 1.02E-01 -2.28E+00 /Natural gas/ - - - - - 

YES Gas 1 42 LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #3 9/12/2000 5.60E+01 4.03E+00 /Natural gas/ - - - - - 

YES Gas 1 43 TXValeroTexasCity Heater 45 CO Sample #1 4/3/2001 ND 1.05E-01 -2.26E+00 /Refinery gas/ - - - - - 

YES Gas 1 43 TXValeroTexasCity Heater 45 CO Sample #2 4/3/2001 ND 1.09E-01 -2.22E+00 /Refinery gas/ - - - - - YES Gas 1 43 TXValeroTexasCity Heater 45 CO Sample #3 4/3/2001 ND 1.10E-01 -2.20E+00 /Refinery gas/ - - - - - YES Gas 1 44 MSChevronPascagoula F-8400 CO Sample #1 11/7/2007 1.08E-01 -2.22E+00 /Refinery gas/ - - - - - YES Gas 1 44 MSChevronPascagoula F-8400 CO Sample #2 11/7/2007 1.08E-01 -2.22E+00 /Refinery gas/ - - - - - YES Gas 1 44 MSChevronPascagoula F-8400 CO Sample #3 11/7/2007 1.13E-01 -2.18E+00 /Refinery gas/ - - - - - YES Gas 1 45 TXValeroTexasCity Heater 46 CO Sample #1 4/4/2001 ND 1.10E-01 -2.21E+00 /Refinery gas/ - - - - - YES Gas 1 45 TXValeroTexasCity Heater 46 CO Sample #2 4/4/2001 ND 1.09E-01 -2.22E+00 /Refinery gas/ - - - - - YES Gas 1 45 TXValeroTexasCity Heater 46 CO Sample #3 4/4/2001 ND 1.10E-01 -2.20E+00 /Refinery gas/ - - - - - YES Gas 1 46 KYCatlettsburgRefining 2-30-B-1 CO Sample #1 8/10/2005 ND 1.14E-01 -2.18E+00 /Refinery gas/ - - - - - YES Gas 1 46 KYCatlettsburgRefining 2-30-B-1 CO Sample #1 4/23/2004 5.27E-01 -6.40E-01 /Refinery gas/ - - - - - YES Gas 1 46 KYCatlettsburgRefining 2-30-B-1 CO Sample #2 8/10/2005 ND 1.17E-01 -2.15E+00 /Refinery gas/ - - - - - YES Gas 1 46 KYCatlettsburgRefining 2-30-B-1 CO Sample #3 8/10/2005 ND 1.19E-01 -2.13E+00 /Refinery gas/ - - - - - YES Gas 1 47 LAShellChemicaGeismar

Furnace FS2801 CO Sample #1 2/14/2006 ND 1.01E-01 -2.29E+00 /Heavy Recycle/Natural gas/Petrochemical process gas/ - - - - - 

YES Gas 1 47 LAShellChemicaGeismar

Furnace FS2801 CO Sample #2 2/14/2006 ND 1.19E-01 -2.13E+00 /Heavy Recycle/Natural gas/Petrochemical process gas/ - - - - - 

YES Gas 1 47 LAShellChemicaGeismar

Furnace FS2801 CO Sample #3 2/14/2006 ND 1.33E-01 -2.02E+00 /Heavy Recycle/Natural gas/Petrochemical process gas/ - - - - - 

YES Gas 1 48 KYCatlettsburgRefining 2-23-B-3 CO Sample #1 8/16/2005 ND 1.19E-01 -2.13E+00 /Refinery gas/ - - - - - 

YES Gas 1 48 KYCatlettsburgRefining 2-23-B-3 CO Sample #2 8/16/2005 ND 1.17E-01 -2.14E+00 /Refinery gas/ - - - - - YES Gas 1 48 KYCatlettsburgRefining 2-23-B-3 CO Sample #3 8/16/2005 ND 1.18E-01 -2.13E+00 /Refinery gas/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 49 TXRohmHaasDeerPark N-13 CO Sample #1 11/8/2006 1.20E-01 -2.12E+00 /Natural gas/ - - - - - 

YES Gas 1 49 TXRohmHaasDeerPark N-13 CO Sample #2 11/8/2006 1.20E-01 -2.12E+00 /Natural gas/ - - - - - YES Gas 1 49 TXRohmHaasDeerPark N-13 CO Sample #3 11/8/2006 1.20E-01 -2.12E+00 /Natural gas/ - - - - - YES Gas 1 50 TXWesternRefining F-4150 CO Sample #1 8/26/2005 1.22E-01 -2.11E+00 /Refinery gas/ - - - - - 

YES Gas 1 50 TXWesternRefining F-4150 CO Sample #2 8/26/2005 1.22E-01 -2.11E+00 /Refinery gas/ - - - - - YES Gas 1 50 TXWesternRefining F-4150 CO Sample #3 8/26/2005 1.22E-01 -2.11E+00 /Refinery gas/ - - - - - YES Gas 1 51 TXWesternRefining F-4160 CO Sample #1 8/26/2005 1.22E-01 -2.11E+00 /Refinery gas/ - - - - - YES Gas 1 51 TXWesternRefining F-4160 CO Sample #2 8/26/2005 1.22E-01 -2.11E+00 /Refinery gas/ - - - - - YES Gas 1 51 TXWesternRefining F-4160 CO Sample #3 8/26/2005 1.22E-01 -2.11E+00 /Refinery gas/ - - - - - YES Gas 1 52 TXValeroTexasCity Heater 57 CO Sample #1 1/28/2004 ND 1.27E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 52 TXValeroTexasCity Heater 57 CO Sample #2 1/28/2004 ND 1.28E-01 -2.06E+00 /Refinery gas/ - - - - - YES Gas 1 52 TXValeroTexasCity Heater 57 CO Sample #3 1/28/2004 ND 1.28E-01 -2.06E+00 /Refinery gas/ - - - - - YES Gas 1 53 MSChevronPascagoula F-2440 CO Sample #1 5/15/2007 9.53E-02 -2.35E+00 /Refinery gas/ - - - - - YES Gas 1 53 MSChevronPascagoula F-2440 CO Sample #2 5/15/2007 1.26E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 53 MSChevronPascagoula F-2440 CO Sample #3 5/15/2007 1.61E-01 -1.82E+00 /Refinery gas/ - - - - - YES Gas 1 54 MSChevronPascagoula F-2450 CO Sample #1 5/15/2007 9.53E-02 -2.35E+00 /Refinery gas/ - - - - - YES Gas 1 54 MSChevronPascagoula F-2450 CO Sample #2 5/15/2007 1.26E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 54 MSChevronPascagoula F-2450 CO Sample #3 5/15/2007 1.61E-01 -1.82E+00 /Refinery gas/ - - - - - YES Gas 1 55 MSChevronPascagoula F-2460 CO Sample #1 5/15/2007 9.53E-02 -2.35E+00 /Refinery gas/ - - - - - YES Gas 1 55 MSChevronPascagoula F-2460 CO Sample #2 5/15/2007 1.26E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 55 MSChevronPascagoula F-2460 CO Sample #3 5/15/2007 1.61E-01 -1.82E+00 /Refinery gas/ - - - - - YES Gas 1 56 MSChevronPascagoula F-2470 CO Sample #1 5/15/2007 9.53E-02 -2.35E+00 /Refinery gas/ - - - - - YES Gas 1 56 MSChevronPascagoula F-2470 CO Sample #2 5/15/2007 1.26E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 56 MSChevronPascagoula F-2470 CO Sample #3 5/15/2007 1.61E-01 -1.82E+00 /Refinery gas/ - - - - - YES Gas 1 57 MSChevronPascagoula F-2480 CO Sample #1 5/15/2007 9.53E-02 -2.35E+00 /Refinery gas/ - - - - - YES Gas 1 57 MSChevronPascagoula F-2480 CO Sample #2 5/15/2007 1.26E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 57 MSChevronPascagoula F-2480 CO Sample #3 5/15/2007 1.61E-01 -1.82E+00 /Refinery gas/ - - - - - YES Gas 1 58 MSChevronPascagoula F-2490 CO Sample #1 5/15/2007 9.53E-02 -2.35E+00 /Refinery gas/ - - - - - YES Gas 1 58 MSChevronPascagoula F-2490 CO Sample #2 5/15/2007 1.26E-01 -2.07E+00 /Refinery gas/ - - - - - YES Gas 1 58 MSChevronPascagoula F-2490 CO Sample #3 5/15/2007 1.61E-01 -1.82E+00 /Refinery gas/ - - - - - YES Gas 1 59 WAConocoPhillipsFerndale 38F-101 CO Sample #1 1/10/2008 ND 1.29E-01 -2.05E+00 /Natural gas/ - - - - - 

YES Gas 1 59 WAConocoPhillipsFerndale 38F-101 CO Sample #2 1/10/2008 ND 1.29E-01 -2.05E+00 /Natural gas/ - - - - - YES Gas 1 59 WAConocoPhillipsFerndale 38F-101 CO Sample #3 1/10/2008 ND 1.29E-01 -2.05E+00 /Natural gas/ - - - - - YES Gas 1 60 TXValeroTexasCity Heater 58 CO Sample #1 1/29/2004 ND 1.32E-01 -2.02E+00 /Refinery gas/ - - - - - 

YES Gas 1 60 TXValeroTexasCity Heater 58 CO Sample #2 1/29/2004 ND 1.27E-01 -2.06E+00 /Refinery gas/ - - - - - YES Gas 1 60 TXValeroTexasCity Heater 58 CO Sample #3 1/29/2004 ND 1.27E-01 -2.06E+00 /Refinery gas/ - - - - - YES Gas 1 61 TXRohmHaasDeerPark ACET-2B-1 CO Sample #1 11/13/2006 1.23E+00 2.07E-01 /Natural gas/ - - - - - 

YES Gas 1 61 TXRohmHaasDeerPark ACET-2B-1 CO Sample #1 11/14/2006 ND 1.30E-01 -2.04E+00 /Natural gas/ - - - - - YES Gas 1 61 TXRohmHaasDeerPark ACET-2B-1 CO Sample #2 11/13/2006 8.30E-01 -1.86E-01 /Natural gas/ - - - - - YES Gas 1 61 TXRohmHaasDeerPark ACET-2B-1 CO Sample #2 11/14/2006 ND 1.30E-01 -2.04E+00 /Natural gas/ - - - - - YES Gas 1 61 TXRohmHaasDeerPark ACET-2B-1 CO Sample #3 11/14/2006 ND 1.30E-01 -2.04E+00 /Natural gas/ - - - - - YES Gas 1 61 TXRohmHaasDeerPark ACET-2B-1 CO Sample #3 11/13/2006 3.30E-01 -1.11E+00 /Natural gas/ - - - - - YES Gas 1 62 TXValeroTexasCity Heater 18 CO Sample #1 10/15/2002 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - 

YES Gas 1 62 TXValeroTexasCity Heater 18 CO Sample #2 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 62 TXValeroTexasCity Heater 18 CO Sample #3 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 63 TXValeroTexasCity Heater 19 CO Sample #1 10/15/2002 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 63 TXValeroTexasCity Heater 19 CO Sample #2 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 63 TXValeroTexasCity Heater 19 CO Sample #3 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 64 TXValeroTexasCity Heater 20 CO Sample #1 10/15/2002 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 64 TXValeroTexasCity Heater 20 CO Sample #2 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 64 TXValeroTexasCity Heater 20 CO Sample #3 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 65 TXValeroTexasCity Heater 21 CO Sample #1 10/15/2002 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 65 TXValeroTexasCity Heater 21 CO Sample #2 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 65 TXValeroTexasCity Heater 21 CO Sample #3 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 66 TXValeroTexasCity Heater 22 CO Sample #1 10/15/2002 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 66 TXValeroTexasCity Heater 22 CO Sample #2 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 66 TXValeroTexasCity Heater 22 CO Sample #3 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 67 TXValeroTexasCity Heater 23 CO Sample #1 10/15/2002 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 67 TXValeroTexasCity Heater 23 CO Sample #2 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 67 TXValeroTexasCity Heater 23 CO Sample #3 10/15/2002 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 68 TXWesternRefining H-8801 CO Sample #1 5/16/2007 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 68 TXWesternRefining H-8801 CO Sample #2 5/16/2007 7.00E-02 -2.66E+00 /Refinery gas/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 68 TXWesternRefining H-8801 CO Sample #3 5/16/2007 2.30E-01 -1.47E+00 /Refinery gas/ - - - - - 

YES Gas 1 69 TXWesternRefining H-8802 CO Sample #1 5/16/2007 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - YES Gas 1 69 TXWesternRefining H-8802 CO Sample #2 5/16/2007 7.00E-02 -2.66E+00 /Refinery gas/ - - - - - YES Gas 1 69 TXWesternRefining H-8802 CO Sample #3 5/16/2007 2.30E-01 -1.47E+00 /Refinery gas/ - - - - - YES Gas 1 70 IAADMClinton

EUCOG-5 #2 Gas Fired Boiler CO Sample #2 3/7/2008 1.35E-01 -2.00E+00 /Natural gas/ - - - - - 

YES Gas 1 70 IAADMClinton

EUCOG-5 #2 Gas Fired Boiler CO Sample #3 3/10/2008 1.35E-01 -2.00E+00 /Natural gas/ - - - - - 

YES Gas 1 71 TXDeerParkRefinery H31003 CO Sample #1 5/25/2001 ND 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - 

YES Gas 1 71 TXDeerParkRefinery H31003 CO Sample #2 5/25/2001 ND 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 71 TXDeerParkRefinery H31003 CO Sample #3 5/25/2001 ND 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 72 TXDeerParkRefinery H5104 CO Sample #1 5/23/2001 ND 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 72 TXDeerParkRefinery H5104 CO Sample #2 5/23/2001 ND 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 72 TXDeerParkRefinery H5104 CO Sample #3 5/23/2001 ND 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 73 TXLyondellPasadena B-1751 CO Sample #1 1/26/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - 

YES Gas 1 73 TXLyondellPasadena B-1751 CO Sample #2 1/26/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 73 TXLyondellPasadena B-1751 CO Sample #3 1/26/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 74 TXLyondellPasadena B-2890 CO Sample #1 1/24/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 74 TXLyondellPasadena B-2890 CO Sample #2 1/24/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 74 TXLyondellPasadena B-2890 CO Sample #3 1/24/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 75 TXLyondellPasadena B-801 CO Sample #1 3/22/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 75 TXLyondellPasadena B-801 CO Sample #2 3/22/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 75 TXLyondellPasadena B-801 CO Sample #3 3/22/2007 1.35E-01 -2.00E+00 /Natural gas/ - - - - - YES Gas 1 76 TXWesternRefining F-1602 CO Sample #1 8/25/2005 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - 

YES Gas 1 76 TXWesternRefining F-1602 CO Sample #2 8/25/2005 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 76 TXWesternRefining F-1602 CO Sample #3 8/25/2005 1.35E-01 -2.00E+00 /Refinery gas/ - - - - - YES Gas 1 77 TXRohmHaasDeerPark HT-49 CO Sample #1 12/6/2006 ND 1.40E-01 -1.97E+00 /Natural gas/ - - - - - 

YES Gas 1 77 TXRohmHaasDeerPark HT-49 CO Sample #2 12/6/2006 ND 1.40E-01 -1.97E+00 /Natural gas/ - - - - - YES Gas 1 78 TXRohmHaasDeerPark N-12 CO Sample #1 11/7/2006 1.40E-01 -1.97E+00 /Natural gas/ - - - - - YES Gas 1 78 TXRohmHaasDeerPark N-12 CO Sample #2 11/7/2006 1.30E-01 -2.04E+00 /Natural gas/ - - - - - YES Gas 1 78 TXRohmHaasDeerPark N-12 CO Sample #3 11/7/2006 1.50E-01 -1.90E+00 /Natural gas/ - - - - - YES Gas 1 79 LAShellChemicaGeismar

Furnace FS801 CO Sample #1 2/15/2006 ND 1.35E-01 -2.01E+00 /Heavy Recycle/Natural gas/Petrochemical process gas/ - - - - - 

YES Gas 1 79 LAShellChemicaGeismar

Furnace FS801 CO Sample #2 2/15/2006 ND 1.43E-01 -1.94E+00 /Heavy Recycle/Natural gas/Petrochemical process gas/ - - - - - 

YES Gas 1 79 LAShellChemicaGeismar

Furnace FS801 CO Sample #3 2/15/2006 ND 1.43E-01 -1.94E+00 /Heavy Recycle/Natural gas/Petrochemical process gas/ - - - - - 

YES Gas 1 80 DEDuPontEdgemoor RX-9 CO Sample #1 6/28/2007 ND 1.05E-01 -2.25E+00 /Natural gas/ - - - - - 

YES Gas 1 80 DEDuPontEdgemoor RX-9 CO Sample #2 6/28/2007 1.05E-01 -2.25E+00 /Natural gas/ - - - - - YES Gas 1 80 DEDuPontEdgemoor RX-9 CO Sample #3 6/28/2007 2.11E-01 -1.56E+00 /Natural gas/ - - - - - YES Gas 1 81 PANorfolkSouthern Boiler 1 CO Sample #1 10/19/2006 4.56E+00 1.52E+00 /Natural gas/ - - - - - YES Gas 1 81 PANorfolkSouthern Boiler 1 CO Sample #2 10/19/2006 8.00E-02 -2.53E+00 /Natural gas/ - - - - - YES Gas 1 81 PANorfolkSouthern Boiler 1 CO Sample #2 10/19/2006 2.53E+00 9.28E-01 /Natural gas/ - - - - - YES Gas 1 81 PANorfolkSouthern Boiler 1 CO Sample #3 10/19/2006 1.50E-01 -1.90E+00 /Natural gas/ - - - - - YES Gas 1 81 PANorfolkSouthern Boiler 1 CO Sample #3 10/19/2006 1.08E+00 7.70E-02 /Natural gas/ - - - - - YES Gas 1 81 PANorfolkSouthern Boiler 1 CO Sample #3 10/19/2006 2.58E+00 9.48E-01 /Natural gas/ - - - - - YES Gas 1 82 TXWesternRefining 109 CO Sample #1 2/28/2006 4.59E-02 -3.08E+00 /Refinery gas/ - - - - - 

YES Gas 1 82 TXWesternRefining 109 CO Sample #2 2/28/2006 1.95E-01 -1.63E+00 /Refinery gas/ - - - - - YES Gas 1 82 TXWesternRefining 109 CO Sample #3 2/28/2006 2.31E-01 -1.47E+00 /Refinery gas/ - - - - - YES Gas 1 83 TXRohmHaasDeerPark ACET-2A-1 CO Sample #1 11/14/2006 1.70E-01 -1.77E+00 /Refinery gas/ - - - - - YES Gas 1 83 TXRohmHaasDeerPark ACET-2A-1 CO Sample #1 11/13/2006 4.71E+00 1.55E+00 /Natural gas/ - - - - - 

YES Gas 1 83 TXRohmHaasDeerPark ACET-2A-1 CO Sample #2 11/14/2006 1.50E-01 -1.90E+00 /Refinery gas/ - - - - - 

YES Gas 1 83 TXRohmHaasDeerPark ACET-2A-1 CO Sample #2 11/13/2006 7.42E+00 2.00E+00 /Natural gas/ - - - - - 

YES Gas 1 83 TXRohmHaasDeerPark ACET-2A-1 CO Sample #3 11/14/2006 1.80E-01 -1.71E+00 /Refinery gas/ - - - - - 

YES Gas 1 83 TXRohmHaasDeerPark ACET-2A-1 CO Sample #3 11/13/2006 6.56E+00 1.88E+00 /Natural gas/ - - - - - 

YES Gas 1 84 TXValeroCorpusChristi 154-H-1 CO Sample #1 5/20/2008 ND 1.00E-01 -2.30E+00 /Refinery gas/ - - - - - 

YES Gas 1 84 TXValeroCorpusChristi 154-H-1 CO Sample #2 5/20/2008 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 84 TXValeroCorpusChristi 154-H-1 CO Sample #3 5/20/2008 2.00E-01 -1.61E+00 /Refinery gas/ - - - - - YES Gas 1 85 MSChevronPascagoula F-6410 CO Sample #1 12/6/2007 6.27E-02 -2.77E+00 /Refinery gas/ - - - - - YES Gas 1 85 MSChevronPascagoula F-6410 CO Sample #2 12/6/2007 6.33E-02 -2.76E+00 /Refinery gas/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 85 MSChevronPascagoula F-6410 CO Sample #3 12/6/2007 3.78E-01 -9.74E-01 /Refinery gas/ - - - - - 

YES Gas 1 86 KYCatlettsburgRefining 2-36-B-1 CO Sample #1 6/23/2004 ND 3.12E+00 1.14E+00 /Refinery gas/ - - - - - YES Gas 1 86 KYCatlettsburgRefining 2-36-B-1 CO Sample #1 9/14/2005 ND 1.69E-01 -1.78E+00 /Refinery gas/ - - - - - YES Gas 1 86 KYCatlettsburgRefining 2-36-B-1 CO Sample #2 9/14/2005 ND 1.69E-01 -1.78E+00 /Refinery gas/ - - - - - YES Gas 1 86 KYCatlettsburgRefining 2-36-B-1 CO Sample #2 6/23/2004 ND 3.14E+00 1.14E+00 /Refinery gas/ - - - - - YES Gas 1 86 KYCatlettsburgRefining 2-36-B-1 CO Sample #3 6/23/2004 ND 3.17E+00 1.15E+00 /Refinery gas/ - - - - - YES Gas 1 86 KYCatlettsburgRefining 2-36-B-1 CO Sample #3 9/14/2005 ND 1.69E-01 -1.78E+00 /Refinery gas/ - - - - - YES Gas 1 87 OKConocoPhillipsPoncaCity H-0048 CO Sample #1 4/7/2005 2.20E-01 -1.51E+00 /Refinery gas/ - - - - - YES Gas 1 87 OKConocoPhillipsPoncaCity H-0048 CO Sample #2 4/7/2005 1.60E-01 -1.83E+00 /Refinery gas/ - - - - - YES Gas 1 87 OKConocoPhillipsPoncaCity H-0048 CO Sample #3 4/7/2005 1.30E-01 -2.04E+00 /Refinery gas/ - - - - - YES Gas 1 88 MTMontanaRefining

H-1801 Hydrogen Plant Heater CO Sample #1 9/20/2007 1.71E-01 -1.76E+00 /Natural gas/ - - - - - 

YES Gas 1 88 MTMontanaRefining

H-1801 Hydrogen Plant Heater CO Sample #2 9/20/2007 8.57E-02 -2.46E+00 /Natural gas/ - - - - - 

YES Gas 1 88 MTMontanaRefining

H-1801 Hydrogen Plant Heater CO Sample #3 9/20/2007 2.57E-01 -1.36E+00 /Natural gas/ - - - - - 

YES Gas 1 89 TXRohmHaasDeerPark ACET-2A-3 CO Sample #1 11/28/2006 4.00E-01 -9.16E-01 /Refinery gas/ - - - - - 

YES Gas 1 89 TXRohmHaasDeerPark ACET-2A-3 CO Sample #1 11/27/2006 3.70E-01 -9.94E-01 /Natural gas/ - - - - - 

YES Gas 1 89 TXRohmHaasDeerPark ACET-2A-3 CO Sample #2 11/28/2006 4.30E-01 -8.44E-01 /Refinery gas/ - - - - - 

YES Gas 1 89 TXRohmHaasDeerPark ACET-2A-3 CO Sample #2 11/27/2006 8.00E-02 -2.53E+00 /Natural gas/ - - - - - 

YES Gas 1 89 TXRohmHaasDeerPark ACET-2A-3 CO Sample #3 11/28/2006 3.40E-01 -1.08E+00 /Refinery gas/ - - - - - 

YES Gas 1 89 TXRohmHaasDeerPark ACET-2A-3 CO Sample #3 11/27/2006 8.00E-02 -2.53E+00 /Natural gas/ - - - - - 

YES Gas 1 90 MSChevronPascagoula F-8300B CO Sample #1 3/2/2007 7.88E-02 -2.54E+00 /Refinery gas/ - - - - - 

YES Gas 1 90 MSChevronPascagoula F-8300B CO Sample #2 3/2/2007 7.90E-02 -2.54E+00 /Refinery gas/ - - - - - YES Gas 1 90 MSChevronPascagoula F-8300B CO Sample #3 3/2/2007 3.96E-01 -9.27E-01 /Refinery gas/ - - - - - YES Gas 1 91 VAUniversityofVirginia 7103-1-01R CO Sample #1 12/5/2007 2.60E-01 -1.35E+00 /Natural gas/ - - - - - 

YES Gas 1 91 VAUniversityofVirginia 7103-1-01R CO Sample #2 12/5/2007 1.30E-01 -2.04E+00 /Natural gas/ - - - - - YES Gas 1 y 1 INNucorSteel

Cold Mill Annealing CO Sample #1 6/24/2004 1.75E-01 -1.74E+00 /Natural gas/ - - - - - 

YES Gas 1 y 1 INNucorSteel

Cold Mill Annealing CO Sample #2 8/19/2009 9.01E-02 -2.41E+00 Natural gas - - - - - 

YES Gas 1 y 2 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-1 8/12/2009 5.68E-01 -5.66E-01 Natural gas - - - - - 

YES Gas 1 y 2 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-3 8/13/2009 1.48E-01 -1.91E+00 Natural gas - - - - - 

YES Gas 1 y 2 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-4 8/13/2009 4.36E-01 -8.30E-01 Natural gas - - - - - 

YES Gas 1 y 2 CORockyMtnSteel212

Rod/Bar Mill Furnace 

95OPPB088 CO M10-6 8/14/2009 8.59E-01 -1.52E-01 Natural gas - - - - - 

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801 CO 1 8/25/2009 ND 1.29E-02 -4.35E+00 Heavy Recycle/Natural gas/Petrochemical process gas

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801 CO 2 8/25/2009 ND 1.29E-02 -4.35E+00 Heavy Recycle/Natural gas/Petrochemical process gas

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801 CO 3 8/26/2009 ND 1.29E-02 -4.35E+00 Heavy Recycle/Natural gas/Petrochemical process gas

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801 CO 4 8/26/2009 ND 1.29E-02 -4.35E+00 Heavy Recycle/Natural gas/Petrochemical process gas

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801 CO 5 8/27/2009 ND 1.29E-02 -4.35E+00 Heavy Recycle/Natural gas/Petrochemical process gas

YES Gas 2 1 LAShellChemicaGeismar

Furnace FS801 CO 6 8/27/2009 ND 1.29E-02 -4.35E+00 Heavy Recycle/Natural gas/Petrochemical process gas

YES Gas 2 2 TXEquistarChemicals UTBLRG CO Sample #1 2/28/2006 2.23E-02 -3.80E+00 /Natural gas/Process gas/
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 2 2 TXEquistarChemicals UTBLRG CO Sample #2 2/28/2006 2.07E-02 -3.88E+00 /Natural gas/Process gas/

YES Gas 2 2 TXEquistarChemicals UTBLRG CO Sample #3 2/28/2006 2.04E-02 -3.89E+00 /Natural gas/Process gas/YES Gas 2 3 TXFlintHillsPortArthur

LOUBOILER10 CO Sample #1 6/10/1998 ND 1.00E-01 -2.30E+00

/Natural gas/Petrochemical process 

gas/

YES Gas 2 3 TXFlintHillsPortArthur

LOUBOILER10 CO Sample #2 6/10/1998 4.00E-02 -3.22E+00

/Natural gas/Petrochemical process 

gas/

YES Gas 2 3 TXFlintHillsPortArthur

LOUBOILER10 CO Sample #3 6/10/1998 ND 1.00E-01 -2.30E+00

/Natural gas/Petrochemical process 

gas/

YES Gas 2 4 TXEquistarChannelview F38001A CO Sample #1 2/16/2004 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - 

YES Gas 2 4 TXEquistarChannelview F38001A CO Sample #2 2/16/2004 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 4 TXEquistarChannelview F38001A CO Sample #3 2/16/2004 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 5 TXEquistarChannelview F38001B CO Sample #1 2/16/2004 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 5 TXEquistarChannelview F38001B CO Sample #2 2/16/2004 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 5 TXEquistarChannelview F38001B CO Sample #3 2/16/2004 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 6 TXFlintHillsPortArthur

LOUBOILER9 CO Sample #1 6/9/1998 ND 1.00E-01 -2.30E+00

/Natural gas/Petrochemical process 

gas/

YES Gas 2 6 TXFlintHillsPortArthur

LOUBOILER9 CO Sample #2 6/9/1998 ND 1.00E-01 -2.30E+00

/Natural gas/Petrochemical process 

gas/

YES Gas 2 6 TXFlintHillsPortArthur

LOUBOILER9 CO Sample #3 6/9/1998 ND 1.00E-01 -2.30E+00

/Natural gas/Petrochemical process 

gas/

YES Gas 2 7 TXLyondellChannelview F6101 CO Sample #1 8/7/2002 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - 

YES Gas 2 7 TXLyondellChannelview F6101 CO Sample #2 8/7/2002 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 7 TXLyondellChannelview F6101 CO Sample #3 8/7/2002 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 8 TXLyondellChannelview F6105 CO Sample #1 8/8/2002 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 8 TXLyondellChannelview F6105 CO Sample #2 8/8/2002 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 8 TXLyondellChannelview F6105 CO Sample #3 8/8/2002 ND 1.00E-01 -2.30E+00 /Process gas/ - - - - - YES Gas 2 9 TXEquistarChannelview F4601 CO Sample #1 2/13/2007 ND 1.10E-01 -2.21E+00 /Process gas/ - - - - - YES Gas 2 9 TXEquistarChannelview F4601 CO Sample #2 2/13/2007 ND 1.10E-01 -2.21E+00 /Process gas/ - - - - - YES Gas 2 9 TXEquistarChannelview F4601 CO Sample #3 2/13/2007 ND 1.10E-01 -2.21E+00 /Process gas/ - - - - - YES Liquid 1 SCDAKAmericas P8F CO Sample #4 7/15/2009 6.43E-02 -2.74E+00 No. 6 Residual oil

YES Liquid 1 SCDAKAmericas P8F CO Sample #5 7/15/2009 3.86E-02 -3.25E+00 No. 6 Residual oil

YES Liquid 2 ORGeorgiaPacificWaunaMill

EU33 - Power Boiler CO Sample #1 3/14/2007 ND 1.25E-01 -2.08E+00 /Natural gas/No. 6 Residual oil/ - - - - 91.47 

YES Liquid 2 ORGeorgiaPacificWaunaMill

EU33 - Power Boiler CO Sample #2 3/14/2007 ND 1.25E-01 -2.08E+00 /Natural gas/No. 6 Residual oil/ - - - - 91.47 

YES Liquid 2 ORGeorgiaPacificWaunaMill

EU33 - Power Boiler CO Sample #3 3/14/2007 ND 1.25E-01 -2.08E+00 /Natural gas/No. 6 Residual oil/ - - - - 91.47 

YES Liquid 3 NJSunocoWestville Boiler #8 CO Sample #1 11/20/2007 ND 1.28E-01 -2.05E+00 /Jet Fuel/ - - - - - 

YES Liquid 3 NJSunocoWestville Boiler #8 CO Sample #2 11/20/2007 ND 1.28E-01 -2.05E+00 /Jet Fuel/ - - - - - YES Liquid 3 NJSunocoWestville Boiler #8 CO Sample #3 11/20/2007 ND 1.28E-01 -2.05E+00 /Jet Fuel/ - - - - - YES Liquid 4 NJSunocoWestville Boiler #7 CO Sample #1 12/19/2005 3.86E-02 -3.25E+00 /Jet Fuel/ - - - - - YES Liquid 4 NJSunocoWestville Boiler #7 CO Sample #2 12/19/2005 2.83E-01 -1.26E+00 /Jet Fuel/ - - - - - YES Liquid 4 NJSunocoWestville Boiler #7 CO Sample #3 12/19/2005 2.70E-01 -1.31E+00 /Jet Fuel/ - - - - - YES Liquid 5 NENebraskaCityStation

Auxiliary Boiler 2 CO Sample #1 6/6/2007 2.80E-01 -1.27E+00 /No. 2 Distillate/ - - - - - 

YES Liquid 5 NENebraskaCityStation

Auxiliary Boiler 2 CO Sample #2 6/6/2007 2.10E-01 -1.56E+00 /No. 2 Distillate/ - - - - - 

YES Liquid 5 NENebraskaCityStation

Auxiliary Boiler 2 CO Sample #3 6/6/2007 3.30E-01 -1.11E+00 /No. 2 Distillate/ - - - - - 

YES Liquid 6 NJSunocoWestville Boiler #5 CO Sample #1 11/16/2007 3.85E-01 -9.55E-01 /Jet Fuel/ - - - - - 

YES Liquid 6 NJSunocoWestville Boiler #5 CO Sample #2 11/16/2007 2.57E-01 -1.36E+00 /Jet Fuel/ - - - - - YES Liquid 6 NJSunocoWestville Boiler #5 CO Sample #3 11/16/2007 2.57E-01 -1.36E+00 /Jet Fuel/ - - - - - YES Liquid 7 SCGPChemRussellville FO Boiler CO Sample #1 8/25/2009 1.03E-01 -2.27E+00 Diesel fuel - - - - - 

YES Liquid 7 SCGPChemRussellville FO Boiler CO Sample #2 8/25/2009 7.72E-02 -2.56E+00 Diesel fuel - - - - - YES Liquid 7 SCGPChemRussellville FO Boiler CO Sample #3 8/25/2009 9.39E-01 -6.25E-02 Diesel fuel - - - - - YES Liquid 8 NJMerckRahway

E750009 - Boiler #9 CO Sample #1 3/14/2008 ND 5.15E-01 -6.64E-01 /No. 2 Distillate/ - - - - - 

YES Liquid 8 NJMerckRahway

E750009 - Boiler #9 CO Sample #2 3/14/2008 ND 5.15E-01 -6.64E-01 /No. 2 Distillate/ - - - - - 
Appendix C-7: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Liquid 8 NJMerckRahway

E750009 - Boiler #9 CO Sample #3 3/14/2008 ND 5.15E-01 -6.64E-01 /No. 2 Distillate/ - - - - - 

YES Liquid 9 OHOSUColumbus B140 CO Sample #1 2/2/2005 ND 5.19E-01 -6.55E-01 /Diesel fuel/Natural gas/

YES Liquid 9 OHOSUColumbus B140 CO Sample #2 2/2/2005 5.93E-01 -5.22E-01 /Diesel fuel/Natural gas/YES Liquid 9 OHOSUColumbus B140 CO Sample #3 2/2/2005 ND 5.21E-01 -6.53E-01 /Diesel fuel/Natural gas/YES Liquid 10 NCCampLejeuneMCB

C-CG-650-84B CO Sample #1 3/18/2008 7.00E-01 -3.57E-01 /Natural gas/No. 2 Distillate/

YES Liquid 10 NCCampLejeuneMCB

C-CG-650-84B CO Sample #2 3/18/2008 8.00E-01 -2.23E-01 /Natural gas/No. 2 Distillate/

YES Liquid 10 NCCampLejeuneMCB

C-CG-650-84B CO Sample #3 3/18/2008 2.00E-01 -1.61E+00 /Natural gas/No. 2 Distillate/

YES Liquid 11 VADominionPossumPoint

Aux. Boiler 001 CO Sample #1 3/11/2008 3.95E-01 -9.30E-01 /No. 2 Distillate/ - - - - - 

YES Liquid 11 VADominionPossumPoint

Aux. Boiler 001 CO Sample #2 3/11/2008 7.71E-01 -2.60E-01 /No. 2 Distillate/ - - - - - 

YES Liquid 11 VADominionPossumPoint

Aux. Boiler 001 CO Sample #3 3/11/2008 7.20E-01 -3.28E-01 /No. 2 Distillate/ - - - - - 

YES Liquid 12

PAKeystonePowerPlantShelocta Aux Boiler A CO Sample #1 6/22/1993 3.03E-01 -1.19E+00 /No. 2 Distillate/ - - - - - 

YES Liquid 12

PAKeystonePowerPlantShelocta Aux Boiler A CO Sample #2 6/22/1993 1.22E+00 1.95E-01 /No. 2 Distillate/ - - - - - 

YES Liquid 13 NJSunocoWestville Boiler #6 CO Sample #1 11/15/2007 8.98E-01 -1.08E-01 /Jet Fuel/ - - - - - 

YES Liquid 13 NJSunocoWestville Boiler #6 CO Sample #2 11/15/2007 7.70E-01 -2.62E-01 /Jet Fuel/ - - - - - YES Liquid 13 NJSunocoWestville Boiler #6 CO Sample #3 11/15/2007 8.98E-01 -1.08E-01 /Jet Fuel/ - - - - - YES Liquid 14 NCCampLejeuneMCB

C-CG-650-83B CO Sample #1 11/6/2007 1.10E+00 9.53E-02 /Natural gas/No. 2 Distillate/

YES Liquid 14 NCCampLejeuneMCB

C-CG-650-83B CO Sample #2 11/6/2007 8.00E-01 -2.23E-01 /Natural gas/No. 2 Distillate/

YES Liquid 14 NCCampLejeuneMCB

C-CG-650-83B CO Sample #3 11/6/2007 7.00E-01 -3.57E-01 /Natural gas/No. 2 Distillate/
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 1/25/2007 8.88E+02 6.79E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 12/30/2003 1.45E+03 7.28E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 1/5/2001 1.79E+01 2.88E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 12/17/1999 6.89E+02 6.54E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 1/5/2006 2.87E+02 5.66E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 11/15/2002 4.67E+02 6.15E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 1/31/2000 5.86E+02 6.37E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 2/4/2005 2.07E+02 5.33E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 2/8/1999 2.08E+02 5.34E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 1/24/2008 2.42E+02 5.49E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 5/3/2005 1.77E+02 5.18E+00

/Bagasse/Wood: Unadulterated Lumber/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. 

Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #1 1/9/2002 3.53E+02 5.87E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 2/8/1999 1.66E+02 5.11E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 1/25/2007 2.82E+02 5.64E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 1/31/2000 6.99E+02 6.55E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 5/3/2005 3.14E+02 5.75E+00

/Bagasse/Wood: Unadulterated Lumber/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 1/5/2001 1.91E+01 2.95E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 1/5/2006 3.18E+02 5.76E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 2/4/2005 2.90E+02 5.67E+00 /Bagasse/ 100.00 - - - - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 1/9/2002 3.98E+02 5.99E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 12/17/1999 1.53E+02 5.03E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 11/15/2002 1.71E+02 5.14E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 1/24/2008 2.76E+02 5.62E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #2 12/30/2003 4.83E+02 6.18E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 1/5/2006 2.22E+02 5.40E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 5/5/2005 1.84E+02 5.21E+00

/Bagasse/Wood: Unadulterated Lumber/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 1/9/2002 7.49E+02 6.62E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 12/30/2003 4.40E+02 6.09E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 1/24/2008 6.10E+02 6.41E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 2/8/1999 2.07E+02 5.33E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. 

Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 1/31/2000 4.24E+02 6.05E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 11/15/2002 1.45E+02 4.98E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 1/5/2001 1.91E+01 2.95E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 12/17/1999 2.56E+02 5.55E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 1/25/2007 1.36E+02 4.92E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 1 FLUSSugarCorp Boiler No. 7 CO Sample #3 2/4/2005 1.42E+02 4.95E+00 /Bagasse/ 100.00 - - - - 

YES Biomass

Dutch Oven/Susp. Burner 2

TXDibollTempleInland PB-44 CO Sample #1 6/29/2007 8.61E+01 4.46E+00 /Wood: Plywood, Particleboard (containing glues or resins)/ - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 2

TXDibollTempleInland PB-44 CO Sample #2 6/29/2007 3.99E+01 3.69E+00 /Wood: Plywood, Particleboard (containing glues or resins)/ - - - 100.00 - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass

Dutch Oven/Susp. Burner 2

TXDibollTempleInland PB-44 CO Sample #3 6/29/2007 8.19E+01 4.41E+00 /Wood: Plywood, Particleboard (containing glues or resins)/ - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #1 6/22/2006 1.72E+03 7.45E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #1 8/11/2009 1.80E+02 5.19E+00 Hog Fuel - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #1 8/11/2009 1.68E+02 5.12E+00 Hog Fuel - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #2 8/11/2009 3.25E+02 5.78E+00 Hog Fuel - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #2 6/22/2006 7.65E+02 6.64E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #2 8/11/2009 3.15E+02 5.75E+00 Hog Fuel - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #3 8/12/2009 2.79E+02 5.63E+00 Hog Fuel - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #3 8/12/2009 2.74E+02 5.61E+00 Hog Fuel - - - 100.00 - 

YES Biomass

Dutch Oven/Susp. Burner 3

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #3 6/22/2006 4.92E+02 6.20E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler CO 2 7/14/2009 2.73E+01 3.31E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 63.71 18.74 

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler CO 3 7/15/2009 3.03E+01 3.41E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 63.71 18.74 

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler CO 4 7/15/2009 2.55E+01 3.24E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 63.71 18.74 

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler CO Sample #1 3/27/2007 2.82E+01 3.34E+00

/Hog Fuel/Industrial Sludge/Natural gas/ - - - 63.71 18.74 

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler CO Sample #2 3/27/2007 2.14E+01 3.06E+00

/Hog Fuel/Industrial Sludge/Natural gas/ - - - 63.71 18.74 

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler CO Sample #3 3/27/2007 2.21E+01 3.10E+00

/Hog Fuel/Industrial Sludge/Natural gas/ - - - 63.71 18.74 

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11CU301 CO Sample #1 8/13/1999 3.60E+01 3.58E+00

/Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark/

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11CU301 CO Sample #1 7/8/2009 1.39E+02 4.94E+00

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11CU301 CO Sample #2 7/9/2009 3.04E+02 5.72E+00

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11CU301 CO Sample #2 8/13/1999 3.60E+01 3.58E+00

/Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark/

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11CU301 CO Sample #3 8/13/1999 4.74E+01 3.86E+00

/Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark/

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11CU301 CO Sample #3 7/10/2009 3.48E+02 5.85E+00

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 

YES Biomass FB 3 TNDomtar2384 HFB1-1 CO 1 9/16/2009 9.10E+01 4.51E+00 Hog Fuel/Industrial Sludge - - - 99.43 0.57 

YES Biomass FB 3 TNDomtar2384 HFB1-1 CO 2 9/16/2009 8.03E+01 4.39E+00 Hog Fuel/Industrial Sludge - - - 99.43 0.57 

YES Biomass FB 3 TNDomtar2384 HFB1-1 CO 3 9/17/2009 7.39E+01 4.30E+00 Hog Fuel/Industrial Sludge - - - 99.43 0.57 

YES Biomass FB 4

GATempleInlandRome WF CO Sample #1 7/29/2009 1.36E+02 4.91E+00 Wood: Bark - - 100.00 - - 

YES Biomass FB 4

GATempleInlandRome WF CO Sample #1 7/22/2008 7.54E+01 4.32E+00

/Industrial Sludge/Tire Derived 

Fuel (TDF)/Used Petroleumbased Oils (on-spec)/Wood: Bark/

YES Biomass FB 4

GATempleInlandRome WF CO Sample #2 7/29/2009 6.09E+01 4.11E+00 Wood: Bark - - 100.00 - - 

YES Biomass FB 4

GATempleInlandRome WF CO Sample #2 7/22/2008 1.47E+02 4.99E+00

/Industrial Sludge/Tire Derived 

Fuel (TDF)/Used Petroleumbased Oils (on-spec)/Wood: Bark/

YES Biomass FB 4

GATempleInlandRome WF CO Sample #3 7/30/2009 9.92E+01 4.60E+00 Wood: Bark - - 100.00 - - 

YES Biomass FB 4

GATempleInlandRome WF CO Sample #3 7/22/2008 1.65E+02 5.11E+00

/Industrial Sludge/Tire Derived 

Fuel (TDF)/Used Petroleumbased Oils (on-spec)/Wood: Bark/

YES Biomass FB 5

KYDomtarHawesville

Biofuel Boiler B-900 CO Sample #1 12/18/1998 1.27E+02 4.84E+00 /Hog Fuel/Natural gas/ - - - 84.75 - 

YES Biomass FB 5

KYDomtarHawesville

Biofuel Boiler B-900 CO Sample #2 12/18/1998 1.05E+02 4.65E+00 /Hog Fuel/Natural gas/ - - - 84.75 - 

YES Biomass FB 5

KYDomtarHawesville

Biofuel Boiler B-900 CO Sample #3 12/18/1998 1.03E+02 4.64E+00 /Hog Fuel/Natural gas/ - - - 84.75 - 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #1 6/18/2008 5.87E+01 4.07E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #1 6/19/2008 5.36E+01 3.98E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #2 6/19/2008 1.30E+02 4.87E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #2 6/18/2008 5.61E+01 4.03E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #2 6/18/2008 1.72E+02 5.15E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #3 6/19/2008 6.25E+01 4.14E+00 /Hog Fuel/ - - - 100.00 - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #3 6/18/2008 2.33E+02 5.45E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #1 6/19/2008 5.36E+01 3.98E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #1 6/18/2008 5.87E+01 4.07E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #2 6/18/2008 5.61E+01 4.03E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #2 6/18/2008 1.72E+02 5.15E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #2 6/19/2008 1.30E+02 4.87E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #3 6/18/2008 2.33E+02 5.45E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #3 6/19/2008 6.25E+01 4.14E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 8/11/2009 4.98E+01 3.91E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 7/17/2009 7.67E+01 4.34E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 9/28/2004 7.13E+01 4.27E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuser

DierksMill SN-45 CO Sample #1 12/3/2003 1.90E+02 5.25E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 7/17/2009 3.45E+01 3.54E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 8/12/2009 2.03E+02 5.31E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 12/3/2003 2.50E+02 5.52E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 9/28/2004 6.45E+01 4.17E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 8/12/2009 1.61E+02 5.08E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 9/28/2004 6.21E+01 4.13E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 7/20/2009 7.51E+01 4.32E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 12/3/2003 2.75E+02 5.62E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #1 8/12/2009 1.55E+02 5.04E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #1 11/10/2004 1.19E+02 4.78E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuse

r_Raymond

Hog Fuel Boiler EU1 CO Sample #1 9/18/1996 1.10E+02 4.70E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #2 8/13/2009 3.10E+02 5.74E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #2 9/18/1996 1.26E+02 4.83E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #2 11/10/2004 1.18E+02 4.77E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #3 11/10/2004 1.12E+02 4.72E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #3 8/13/2009 3.09E+02 5.73E+00 Hog Fuel - - - 100.00 - 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #3 9/18/1996 1.43E+02 4.96E+00 /Hog Fuel/ - - - 100.00 - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass Fuel Cell 5

WVGPMtHopeOSB

5600 - Wellons Energy System CO Sample #1 7/11/2006 6.76E+01 4.21E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 5

WVGPMtHopeOSB

5600 - Wellons Energy System CO Sample #2 7/11/2006 2.23E+02 5.41E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass Fuel Cell 5

WVGPMtHopeOSB

5600 - Wellons Energy System CO Sample #3 7/11/2006 9.04E+01 4.50E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 1

GATempleInlandThomson BW-B001 CO Sample #1 1/30/2003 5.49E+00 1.70E+00

/Wood: Plywood, Particleboard 

(containing glues or resins)/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 1

GATempleInlandThomson BW-B001 CO Sample #1 12/7/2004 8.16E+02 6.70E+00

/Wood: Plywood, Particleboard 

(containing glues or resins)/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 1

GATempleInlandThomson BW-B001 CO Sample #2 1/30/2003 1.40E+00 3.39E-01

/Wood: Plywood, Particleboard 

(containing glues or resins)/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 1

GATempleInlandThomson BW-B001 CO Sample #2 12/7/2004 1.91E+03 7.56E+00

/Wood: Plywood, Particleboard 

(containing glues or resins)/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 1

GATempleInlandThomson BW-B001 CO Sample #3 12/7/2004 2.78E+03 7.93E+00

/Wood: Plywood, Particleboard 

(containing glues or resins)/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 1

GATempleInlandThomson BW-B001 CO Sample #3 1/30/2003 5.36E+00 1.68E+00

/Wood: Plywood, Particleboard 

(containing glues or resins)/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 2

WVWeyerhaeuserBuckhannon 001-01 CO Sample #1 8/23/2005 4.23E+01 3.74E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 2

WVWeyerhaeuserBuckhannon 001-01 CO Sample #2 8/23/2005 1.36E+01 2.61E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 2

WVWeyerhaeuserBuckhannon 001-01 CO Sample #3 8/23/2005 1.25E+01 2.53E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 3

WAKimberlyClarkEverett

No. 14 Cogeneration Boiler CO 1 8/18/2009 6.71E+01 4.21E+00 Hog Fuel/Natural gas - - - 78.83 - 

YES Biomass

Stoker/SlopedGrate/Other 3

WAKimberlyClarkEverett

No. 14 Cogeneration Boiler CO 2 8/18/2009 4.23E+00 1.44E+00 Hog Fuel/Natural gas - - - 78.83 - 

YES Biomass

Stoker/SlopedGrate/Other 3

WAKimberlyClarkEverett

No. 14 Cogeneration Boiler CO 3 8/19/2009 3.05E+01 3.42E+00 Hog Fuel/Natural gas - - - 78.83 - 

YES Biomass

Stoker/SlopedGrate/Other 4

IDChilcoLakeSawmill HFB1 CO Sample #1 3/30/2005 5.44E+01 4.00E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 4

IDChilcoLakeSawmill HFB1 CO Sample #2 3/30/2005 4.77E+01 3.86E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 4

IDChilcoLakeSawmill HFB1 CO Sample #3 3/30/2005 5.10E+01 3.93E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass

Stoker/SlopedGrate/Other 5

ARWestFraserHuttig SN-24 CO Sample #1 3/1/2005 6.21E+01 4.13E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 5

ARWestFraserHuttig SN-24 CO Sample #2 3/1/2005 7.66E+01 4.34E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 5

ARWestFraserHuttig SN-24 CO Sample #3 3/1/2005 5.57E+01 4.02E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 6 MILPCSagola TOH-Wood CO Sample #1 3/12/2008 5.18E+01 3.95E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 6 MILPCSagola TOH-Wood CO Sample #2 3/12/2008 5.61E+01 4.03E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 6 MILPCSagola TOH-Wood CO Sample #3 3/12/2008 9.60E+01 4.56E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 7

INConsolidatedGrainandBarge P17B CO Sample #1 3/5/2008 7.14E+01 4.27E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 7

INConsolidatedGrainandBarge P17B CO Sample #2 3/5/2008 1.11E+02 4.71E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 7

INConsolidatedGrainandBarge P17B CO Sample #3 3/5/2008 7.91E+01 4.37E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 8

INConsolidatedGrainandBarge P17C CO Sample #1 3/5/2008 7.14E+01 4.27E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 8

INConsolidatedGrainandBarge P17C CO Sample #2 3/5/2008 1.11E+02 4.71E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 8

INConsolidatedGrainandBarge P17C CO Sample #3 3/5/2008 7.91E+01 4.37E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #1 6/16/2007 1.61E+02 5.08E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 87.59 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #1 4/22/2008 8.60E+01 4.45E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #1 4/23/2008 1.29E+02 4.86E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #2 4/22/2008 9.19E+01 4.52E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #2 6/16/2007 2.36E+02 5.47E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 87.59 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #2 4/23/2008 1.08E+02 4.68E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #3 6/16/2007 9.05E+01 4.51E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 87.59 - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #3 4/23/2008 1.23E+02 4.81E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

YES Biomass

Stoker/SlopedGrate/Other 9

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #3 4/22/2008 9.96E+01 4.60E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #1 4/22/2008 9.29E+01 4.53E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #1 4/23/2008 1.30E+02 4.87E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #1 6/16/2007 1.61E+02 5.08E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 87.59 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #2 4/22/2008 9.77E+01 4.58E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #2 6/16/2007 2.36E+02 5.47E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 87.59 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #2 4/23/2008 1.06E+02 4.66E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #3 6/16/2007 9.05E+01 4.51E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 87.59 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #3 4/23/2008 1.23E+02 4.81E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 93.13 - 

YES Biomass

Stoker/SlopedGrate/Other 10

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #3 4/22/2008 1.08E+02 4.69E+00

/Natural gas/Wood: Unadulterated Lumber/ - - - 92.11 - 

YES Biomass

Stoker/SlopedGrate/Other 11

MSGPNewAugusta

AA-015 Power Boiler CO Sample #1 9/12/2007 5.46E+01 4.00E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 11

MSGPNewAugusta

AA-015 Power Boiler CO Sample #2 9/12/2007 4.12E+01 3.72E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 11

MSGPNewAugusta

AA-015 Power Boiler CO Sample #3 9/12/2007 2.10E+02 5.35E+00 /Hog Fuel/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO 1 10/28/2009 1.28E+02 4.86E+00 Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 83.68 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO 2 10/29/2009 1.10E+02 4.70E+00 Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 83.68 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO 3 10/29/2009 1.00E+02 4.61E+00 Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 83.68 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO Sample #1 9/28/2005 3.68E+02 5.91E+00 /Tire Derived Fuel (TDF)/Wood: Bark/ - - 87.59 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO Sample #1 9/29/2008 2.95E+02 5.69E+00 /Wood: Bark/ - - 100.00 - - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO Sample #2 9/29/2008 3.32E+02 5.80E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO Sample #2 9/28/2005 2.37E+02 5.47E+00 /Tire Derived Fuel (TDF)/Wood: Bark/ - - 87.59 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO Sample #3 9/29/2008 3.19E+02 5.77E+00 /Wood: Bark/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 12

KYNewPageWickliffe B09 CO Sample #3 9/28/2005 1.90E+02 5.25E+00 /Tire Derived Fuel (TDF)/Wood: Bark/ - - 87.59 - - 

YES Biomass

Stoker/SlopedGrate/Other 13

ALMeadwestvacoCottonton46

No.3 Wood Residue Boiler CO Sample #1 11/1/2007 1.21E+02 4.79E+00 /Natural gas/Wood: Bark/

YES Biomass

Stoker/SlopedGrate/Other 13

ALMeadwestvacoCottonton46

No.3 Wood Residue Boiler CO Sample #2 11/1/2007 1.21E+02 4.80E+00 /Natural gas/Wood: Bark/

YES Biomass

Stoker/SlopedGrate/Other 13

ALMeadwestvacoCottonton46

No.3 Wood Residue Boiler CO Sample #3 11/1/2007 1.24E+02 4.82E+00 /Natural gas/Wood: Bark/

YES Biomass

Stoker/SlopedGrate/Other 14

MSShuqualakLumber

Boiler 4 (AA108) CO Sample #2 10/20/2006 1.22E+02 4.81E+00 /Wood: Unadulterated Lumber/ - - - 100.00 - 

YES Biomass

Stoker/SlopedGrate/Other 15

MSHoodBeaumont

AA-030 (Wood-Fired Boiler) CO Sample #1 6/22/2006 1.09E+02 4.69E+00

/Hog Fuel/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 15

MSHoodBeaumont

AA-030 (Wood-Fired Boiler) CO Sample #1 5/21/2008 3.28E+02 5.79E+00

/Hog Fuel/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 15

MSHoodBeaumont

AA-030 (Wood-Fired Boiler) CO Sample #2 6/22/2006 1.29E+02 4.86E+00

/Hog Fuel/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 15

MSHoodBeaumont

AA-030 

(Wood-Fired Boiler) CO Sample #2 5/21/2008 4.59E+02 6.13E+00

/Hog Fuel/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 15

MSHoodBeaumont

AA-030 (Wood-Fired Boiler) CO Sample #3 5/21/2008 4.84E+02 6.18E+00

/Hog Fuel/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 100.00 - - 

YES Biomass

Stoker/SlopedGrate/Other 15

MSHoodBeaumont

AA-030 (Wood-Fired Boiler) CO Sample #3 6/22/2006 1.48E+02 4.99E+00

/Hog Fuel/Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins)/ - - 100.00 - - 

YES Coal FB 1

IAADMCornProcessingCR EU-530 CO Sample #1 11/20/2002 3.20E+00 1.16E+00

/Coal: Bituminous/Coal: Subbituminous/ - 100.00 - - - 

YES Coal FB 1

IAADMCornProcessingCR EU-530 CO Sample #2 11/20/2002 7.38E+00 2.00E+00

/Coal: Bituminous/Coal: Subbituminous/ - 100.00 - - - 

YES Coal FB 1

IAADMCornProcessingCR EU-530 CO Sample #3 11/20/2002 1.42E+01 2.65E+00

/Coal: Bituminous/Coal: Subbituminous/ - 100.00 - - - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal FB 2

MENewPageRumford Cogen#6 CO 1 12/9/2009 1.54E+01 2.74E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

YES Coal FB 2

MENewPageRumford Cogen#6 CO 2 12/10/2009 1.15E+01 2.45E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

YES Coal FB 2

MENewPageRumford Cogen#6 CO 3 12/10/2009 1.68E+01 2.82E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

YES Coal FB 3

MENewPageRumford Cogen#7 CO 1 12/9/2009 1.54E+01 2.74E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

YES Coal FB 3

MENewPageRumford Cogen#7 CO 2 12/10/2009 1.15E+01 2.45E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

YES Coal FB 3

MENewPageRumford Cogen#7 CO 3 12/10/2009 1.68E+01 2.82E+00

/Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ - 10.17 - 58.91 3.29 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #1 3/29/2007 7.79E+01 4.36E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #1 3/30/2007 5.57E-02 -2.89E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #1 3/29/2007 6.07E-02 -2.80E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #2 3/30/2007 5.64E-02 -2.88E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #2 3/29/2007 5.43E-02 -2.91E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #2 3/29/2007 7.59E+01 4.33E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #3 3/29/2007 5.62E-02 -2.88E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #3 3/30/2007 5.38E-02 -2.92E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #3 3/29/2007 7.12E+01 4.27E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 2

ILDukeEnergyTuscola Unit 4 CO Sample #1 3/30/2007 5.57E-02 -2.89E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 2

ILDukeEnergyTuscola Unit 4 CO Sample #2 3/30/2007 5.64E-02 -2.88E+00 /Coal: Bituminous/ - 100.00 - - - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal PC 2

ILDukeEnergyTuscola Unit 4 CO Sample #3 3/30/2007 5.38E-02 -2.92E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #1 3/29/2007 6.07E-02 -2.80E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #1 3/29/2007 7.79E+01 4.36E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #2 3/29/2007 5.43E-02 -2.91E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #2 3/29/2007 7.59E+01 4.33E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #3 3/29/2007 7.12E+01 4.27E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #3 3/29/2007 5.62E-02 -2.88E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 4

VAPhilipMorrisPark500 B2 CO Sample #1 9/21/2005 1.31E+00 2.72E-01 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 4

VAPhilipMorrisPark500 B2 CO Sample #2 9/21/2005 1.32E+00 2.77E-01 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 4

VAPhilipMorrisPark500 B2 CO Sample #3 9/21/2005 1.45E+00 3.69E-01 /Coal: Bituminous/ - 100.00 - - - 

YES Coal PC 5

AZCatalystPaperSnowflake

Power Boiler #2 Coal CO Sample #1 3/24/2006 9.44E-01 -5.76E-02 /Coal: Sub-bituminous/ - 100.00 - - - 

YES Coal PC 5

AZCatalystPaperSnowflake

Power Boiler #2 Coal CO Sample #2 3/24/2006 2.52E+00 9.24E-01 /Coal: Sub-bituminous/ - 100.00 - - - 

YES Coal PC 5

AZCatalystPaperSnowflake

Power Boiler #2 Coal CO Sample #3 3/24/2006 3.22E+00 1.17E+00 /Coal: Sub-bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 1 INNotreDame B-4 CO Sample #1 8/25/2009 3.89E+00 1.36E+00 Coal: Bituminous - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 1 INNotreDame B-4 CO Sample #2 8/25/2009 4.67E+00 1.54E+00 Coal: Bituminous - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 1 INNotreDame B-4 CO Sample #3 8/25/2009 4.32E+00 1.46E+00 Coal: Bituminous - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 2

OHMortonSaltRittman

B002 - CoalFired Boiler #2 CO 1 8/25/2009 1.44E+01 2.67E+00 Coal: Bituminous - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 2

OHMortonSaltRittman

B002 - CoalFired Boiler #2 CO 2 8/26/2009 1.52E+01 2.72E+00 Coal: Bituminous - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 2

OHMortonSaltRittman

B002 - CoalFired Boiler #2 CO 3 8/27/2009 1.46E+01 2.68E+00 Coal: Bituminous - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 3

WVDuPontWashingtonWorks P05 CO Sample #1 11/2/2005 1.55E+01 2.74E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 3

WVDuPontWashingtonWorks P05 CO Sample #2 11/2/2005 1.71E+01 2.84E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 3

WVDuPontWashingtonWorks P05 CO Sample #3 11/3/2005 1.63E+01 2.79E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 4 OHAppletonIdeas

Boiler 4 (B003) CO Sample #1 1/29/2003 1.85E+01 2.92E+00 /Coal: Bituminous/ - 100.00 - - - 
Appendix C-8: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant

_Name TestID

TestDate_co

mmon

NonDetect? ppm @ 3% O2 ln (ppm @ 3% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Coal

Stoker/SlopedGrate/Other 4 OHAppletonIdeas

Boiler 4 (B003) CO Sample #2 1/29/2003 2.02E+01 3.00E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 4 OHAppletonIdeas

Boiler 4 (B003) CO Sample #3 1/29/2003 2.05E+01 3.02E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 5

OHAkronThermalEnergy

Boiler #32 (B001) CO Sample #1 3/1/2007 2.12E+01 3.05E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 5

OHAkronThermalEnergy

Boiler #32 (B001) CO Sample #2 3/1/2007 3.41E+01 3.53E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 5

OHAkronThermalEnergy

Boiler #32 (B001) CO Sample #3 3/1/2007 1.88E+01 2.93E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 6 PABellefieldPlant Boiler 1 CO Sample #1 6/6/2006 2.55E+01 3.24E+00 /CO gas/Coal: Bituminous/ - 99.99 - - - 

YES Coal

Stoker/SlopedGrate/Other 6 PABellefieldPlant Boiler 1 CO Sample #2 6/6/2006 2.55E+01 3.24E+00 /CO gas/Coal: Bituminous/ - 99.99 - - - 

YES Coal

Stoker/SlopedGrate/Other 6 PABellefieldPlant Boiler 1 CO Sample #3 6/6/2006 2.55E+01 3.24E+00 /CO gas/Coal: Bituminous/ - 99.99 - - - 

YES Coal

Stoker/SlopedGrate/Other 7

NCNC_DukeUniversity_Durham 7754-03 CO Sample #1 1/10/2000 2.87E+01 3.36E+00

/Coal: Bituminous/No. 2 Distillate/

YES Coal

Stoker/SlopedGrate/Other 7

NCNC_DukeUniversity_Durham 7754-03 CO Sample #2 1/10/2000 2.67E+01 3.28E+00

/Coal: Bituminous/No. 2 Distillate/

YES Coal

Stoker/SlopedGrate/Other 7

NCNC_DukeUniversity_Durham 7754-03 CO Sample #3 1/10/2000 2.75E+01 3.31E+00

/Coal: Bituminous/No. 2 Distillate/

YES Coal

Stoker/SlopedGrate/Other 8

HIPuuneneSugarMill Boiler 3 CO Sample #1 7/23/2007 3.30E+01 3.50E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 8

HIPuuneneSugarMill Boiler 3 CO Sample #2 7/23/2007 5.57E+01 4.02E+00 /Coal: Bituminous/ - 100.00 - - - 

YES Coal

Stoker/SlopedGrate/Other 8

HIPuuneneSugarMill Boiler 3 CO Sample #3 7/24/2007 2.56E+01 3.24E+00 /Coal: Bituminous/ - 100.00 - - - 
Appendix C-9: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorI

D_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect? ng/dscm @ 7% O2 ln (ng/dscm @ 7% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 1 ILAkzoNobelMorris

B-1 Nebraska Boiler

D/F Total Mass Sample #1 7/29/2009 DLL 6.21E-02 -2.78E+00 Natural gas - - - - - 

 

YES Gas 1 1 ILAkzoNobelMorris

B-1 Nebraska Boiler

D/F Total Mass Sample #2 7/30/2009 BDL 1.51E-01 -1.89E+00 Natural gas - - - - - 

 

YES Gas 1 1 ILAkzoNobelMorris

B-1 Nebraska Boiler

D/F Total Mass Sample #3 7/31/2009 BDL 1.51E-01 -1.89E+00 Natural gas - - - - - 

 

YES Gas 1 yes 1 ILUSSGraniteCity

No. 8 Galvanizing Line Furnace

D/F Total Mass Sample #1 8/25/2009 BDL 1.27E-02 -4.37E+00 Natural gas - - - - - 

 

YES Gas 1 yes 1 ILUSSGraniteCity

No. 8 Galvanizing Line Furnace

D/F Total Mass Sample #2 8/25/2009 DLL 1.27E-02 -4.37E+00 Natural gas - - - - - 

 

YES Gas 1 yes 1 ILUSSGraniteCity

No. 8 Galvanizing Line Furnace

D/F Total Mass Sample #3 8/26/2009 BDL 1.27E-02 -4.37E+00 Natural gas - - - - - 

 

YES Gas 2 1 INTateLyleSagamore 21B501

D/F Total Mass Sample #1 8/25/2009 DLL 6.46E-02 -2.74E+00 Biogas/Natural gas - - - - - 

 

YES Gas 2 1 INTateLyleSagamore 21B501

D/F Total Mass Sample #2 8/26/2009 DLL 2.41E-02 -3.73E+00 Biogas/Natural gas - - - - - 

 

YES Gas 2 1 INTateLyleSagamore 21B501

D/F Total Mass Sample #3 8/27/2009 DLL 4.64E-02 -3.07E+00 Biogas/Natural gas - - - - - 

 

YES Liquid 1 SCMilliken-Dewey D30

D/F Total Mass Sample #1 8/11/2009 BDL 2.18E-05 -1.07E+01 Anhydrides Waste - - - - 100.00 

 

YES Liquid 1 SCMilliken-Dewey D30

D/F Total Mass Sample #2 8/11/2009 BDL 2.18E-05 -1.07E+01 Anhydrides Waste - - - - 100.00 

 

YES Liquid 1 SCMilliken-Dewey D30

D/F Total Mass Sample #3 8/1/2009 BDL 2.18E-05 -1.07E+01 Anhydrides Waste - - - - 100.00 

 

YES Liquid 2

NYConEd59thStStationNewYork Boiler 118

D/F Total Mass Sample #1 8/19/2009 DLL 2.05E-03 -6.19E+00 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 2

NYConEd59thStStationNewYork Boiler 118

D/F Total Mass Sample #2 8/19/2009 DLL 1.93E-03 -6.25E+00 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 2

NYConEd59thStStationNewYork Boiler 118

D/F Total Mass Sample #3 8/19/2009 DLL 1.33E-03 -6.62E+00 No. 6 Residual oil - - - - 100.00 

 

YES Liquid 3 CTElectric Boat EMU 17

D/F Total Mass Sample #1 8/19/2009 9.90E-03 -4.62E+00 No. 4 Fuel oil - - - - - 

 

YES Liquid 3 CTElectric Boat EMU 17

D/F Total Mass Sample #2 8/20/2009 8.80E-03 -4.73E+00 No. 4 Fuel oil - - - - - 

 

YES Liquid 3 CTElectric Boat EMU 17

D/F Total Mass Sample #3 8/20/2009 7.90E-03 -4.84E+00 No. 4 Fuel oil - - - - - 

 
Appendix C-10: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon Non-Detect?

ng/dscm @ 

7% O2

ln (ng/dscm 

@ 7% O2) ND? Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

Light Liquid %

Gas 1%

Gas 2%

Other %

Waste %

YES Biomass

Dutch Oven/Susp. Burner 1 ORFlakeboardEugene Boiler-2

D/F Total Mass M23-1 8/25/2009 DLL 1.76E-01 -1.74E+00 1

Natural gas/Wood: Unadulterated Lumber - - - 30.60 - - 69.40 - - -

YES Biomass

Dutch Oven/Susp. Burner 1 ORFlakeboardEugene Boiler-2

D/F Total Mass M23-2 8/25/2009 DLL 9.37E-02 -2.37E+00 1

Natural gas/Wood: Unadulterated Lumber - - - 30.60 - - 69.40 - - -

YES Biomass

Dutch Oven/Susp. Burner 1 ORFlakeboardEugene Boiler-2

D/F Total Mass M23-3 8/26/2009 DLL 2.19E-01 -1.52E+00 1

Natural gas/Wood: Unadulterated Lumber - - - 30.60 - - 69.40 - - -

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

D/F Total Mass Sample #1 7/14/2009 DLL 2.30E-02 -3.77E+00 1

Hog Fuel/Industrial Sludge/Natural gas - - - 76.28 20.70 - 3.02 - - -

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

D/F Total Mass Sample #2 7/15/2009 DLL 4.25E-02 -3.16E+00 1

Hog Fuel/Industrial Sludge/Natural gas - - - 76.28 20.70 - 3.02 - - -

YES Biomass FB 1

ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

D/F Total Mass Sample #3 7/15/2009 DLL 2.45E-02 -3.71E+00 1

Hog Fuel/Industrial Sludge/Natural gas - - - 76.28 20.70 - 3.02 - - -

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11Cu301

D/F Total Mass Sample #1 7/8/2009 DLL 5.36E-02 -2.93E+00 1

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 - - - 8.61 -

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11Cu301

D/F Total Mass Sample #2 7/9/2009 DLL 8.00E-02 -2.53E+00 1

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 - - - 8.61 -

YES Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11Cu301

D/F Total Mass Sample #3 7/10/2009 DLL 1.93E-01 -1.65E+00 1

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 - - - 8.61 -

YES Biomass FB 3 NDCargillWestFargo

Foster Wheeler Boiler (EU43)

D/F Total Mass Sample #1 8/27/2009 DLL 4.76E-01 -7.42E-01 1 Biomass - - - 100.00 - - - - - -

YES Biomass FB 3 NDCargillWestFargo

Foster Wheeler Boiler (EU43)

D/F Total Mass Sample #2 8/29/2009 DLL 3.57E-02 -3.33E+00 1 Biomass - - - 100.00 - - - - - -

YES Biomass FB 3 NDCargillWestFargo

Foster Wheeler Boiler (EU43)

D/F Total Mass Sample #3 8/29/2009 DLL 3.76E-02 -3.28E+00 1 Biomass - - - 100.00 - - - - - -

YES Biomass FB 4 TNBowaterNewsprint

Bubbling Fluidized Bed Boiler

D/F Total Mass Sample #1 8/5/2009 DLL 1.40E-01 -1.97E+00 1

Biomass/Tire Derived Fuel (TDF)/Wood: Bark - - 93.79 2.59 - - - - 3.62 -

YES Biomass FB 4 TNBowaterNewsprint

Bubbling Fluidized Bed Boiler

D/F Total Mass Sample #2 8/5/2009 DLL 2.20E-01 -1.51E+00 1

Biomass/Tire Derived Fuel (TDF)/Wood: Bark - - 93.79 2.59 - - - - 3.62 -

YES Biomass FB 4 TNBowaterNewsprint

Bubbling Fluidized Bed Boiler

D/F Total Mass Sample #3 8/6/2009 DLL 2.10E-01 -1.56E+00 1

Biomass/Tire Derived Fuel (TDF)/Wood: Bark - - 93.79 2.59 - - - - 3.62 -

YES Biomass FB 5 GATempleInlandRome WF

D/F Total Mass Sample #1 7/29/2009 DLL 1.24E+00 2.13E-01 1 Wood: Bark - - 100.00 - - - - - - -

YES Biomass FB 5 GATempleInlandRome WF

D/F Total Mass Sample #2 7/29/2009 DLL 2.09E-01 -1.56E+00 1 Wood: Bark - - 100.00 - - - - - - -

YES Biomass FB 5 GATempleInlandRome WF

D/F Total Mass Sample #3 7/30/2009 DLL 2.32E-01 -1.46E+00 1 Wood: Bark - - 100.00 - - - - - - -

YES Biomass Fuel Cell 1

ARWeyerhaeuserDierksMill SN-45

D/F Total Mass Sample #1 7/17/2009 DLL 2.01E-02 -3.91E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 1

ARWeyerhaeuserDierksMill SN-45

D/F Total Mass Sample #2 7/17/2009 DLL 3.85E-04 -7.86E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 1

ARWeyerhaeuserDierksMill SN-45

D/F Total Mass Sample #3 7/20/2009 DLL 3.31E-02 -3.41E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 2

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

D/F Total Mass Sample #1 8/12/2009 DLL 3.85E-02 -3.26E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 2

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

D/F Total Mass Sample #2 8/13/2009 3.78E-02 -3.28E+00 0 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 2

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

D/F Total Mass Sample #3 8/13/2009 DLL 1.94E-02 -3.94E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 3 MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

D/F Total Mass Sample #1 8/4/2009 DLL 2.14E-01 -1.54E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 3 MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

D/F Total Mass Sample #2 8/4/2009 DLL 1.36E-01 -2.00E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 3 MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

D/F Total Mass Sample #3 8/4/2009 DLL 1.51E-01 -1.89E+00 1 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 4

ORWeyerhaeuserCoWarrentonLumberMill 3-HFB

D/F Total Mass Sample #2 8/6/2009 3.07E-01 -1.18E+00 0 Hog Fuel - - - 100.00 - - - - - -

YES Biomass Fuel Cell 5 ARAnthonyForestProducts SN-12

D/F Total Mass Sample #1 9/2/2009 DLL 4.97E-01 -6.99E-01 1

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - - - - - -

YES Biomass Fuel Cell 5 ARAnthonyForestProducts SN-12

D/F Total Mass Sample #2 9/2/2009 DLL 3.58E-01 -1.03E+00 1

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - - - - - -

YES Biomass Fuel Cell 5 ARAnthonyForestProducts SN-12

D/F Total Mass Sample #3 9/3/2009 DLL 8.40E-01 -1.75E-01 1

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - - - - - -
Appendix C-10: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common Pollutant TestID

TestDate_co

mmon Non-Detect?

ng/dscm @ 

7% O2

ln (ng/dscm 

@ 7% O2) ND? Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

Light Liquid %

Gas 1%

Gas 2%

Other %

Waste %

YES Biomass

Stoker/SlopedGrate/Other 1 GAGPMadisonPly

800 Wood Waste Boiler

D/F Total Mass Sample #1 8/13/2009 DLL 4.61E-02 -3.08E+00 1 Wood: Bark - - 100.00 - - - - - - -

YES Biomass

Stoker/SlopedGrate/Other 1 GAGPMadisonPly

800 Wood Waste Boiler

D/F Total Mass Sample #2 8/14/2009 DLL 2.22E-02 -3.81E+00 1 Wood: Bark - - 100.00 - - - - - - -

YES Biomass

Stoker/SlopedGrate/Other 1 GAGPMadisonPly

800 Wood Waste Boiler

D/F Total Mass Sample #3 8/14/2009 DLL 1.95E-02 -3.94E+00 1 Wood: Bark - - 100.00 - - - - - - -

YES Biomass

Stoker/SlopedGrate/Other 2 SCMarlboroPaper

Hogged Fuel Boiler

D/F Total Mass Sample #1 7/15/2009 DLL 3.70E-02 -3.30E+00 1

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - - 0.00 - - -

YES Biomass

Stoker/SlopedGrate/Other 2 SCMarlboroPaper

Hogged Fuel Boiler

D/F Total Mass Sample #2 7/15/2009 DLL 4.01E-02 -3.22E+00 1

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard 

(containing glues or resins) - - 95.71 4.29 - - 0.00 - - -

YES Biomass

Stoker/SlopedGrate/Other 2 SCMarlboroPaper

Hogged Fuel Boiler

D/F Total Mass Sample #3 7/15/2009 DLL 4.25E-02 -3.16E+00 1

Industrial Sludge/Wood: Bark/Natural gas/Wood: Plywood, Particleboard (containing glues or resins) - - 95.71 4.29 - - 0.00 - - -

YES Coal FB 1 INPurdueUniverisity Boiler 5

D/F Total Mass Sample #1 7/22/2009 DLL 2.18E-03 -6.13E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal FB 1 INPurdueUniverisity Boiler 5

D/F Total Mass Sample #2 7/23/2009 DLL 1.74E-03 -6.35E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal FB 1 INPurdueUniverisity Boiler 5

D/F Total Mass Sample #3 7/23/2009 DLL 1.82E-03 -6.31E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal FB 2 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

D/F Total Mass Sample #1 6/4/2009 DLL 3.18E-02 -3.45E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal FB 2 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

D/F Total Mass Sample #2 6/5/2009 DLL 1.51E-02 -4.19E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal FB 2 IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

D/F Total Mass Sample #3 6/5/2009 DLL 2.78E-03 -5.89E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal PC 1 WVPPGMartinsville R011-Boiler 3

D/F Total Mass Sample #1 7/22/2009 DLL 2.52E-02 -3.68E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal PC 1 WVPPGMartinsville R011-Boiler 3

D/F Total Mass Sample #2 7/23/2009 DLL 1.41E-02 -4.26E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal PC 1 WVPPGMartinsville R011-Boiler 3

D/F Total Mass Sample #3 7/23/2009 DLL 1.52E-02 -4.18E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal PC 2 NCMillerCoors

ES-2 Coal/No. 2 & 6 Fuel Oil Boiler

D/F Total Mass Sample #1 10/20/2009 DLL 1.91E-02 -3.96E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal PC 2 NCMillerCoors

ES-2 Coal/No. 2 & 6 Fuel Oil Boiler

D/F Total Mass Sample #2 10/20/2009 DLL 1.91E-02 -3.96E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal PC 2 NCMillerCoors

ES-2 Coal/No. 2 & 6 Fuel Oil Boiler

D/F Total Mass Sample #3 10/20/2009 DLL 1.91E-02 -3.96E+00 1 Coal: Bituminous - 100.00 - - - - - - - -

YES Coal

Stoker/SlopedGrate/Other 1 KYISPChemicals 0AA (Riley)

D/F Total Mass Sample #1 11/17/2009 3.20E-03 -5.74E+00 0

Coal: Sub-bituminous/Process coproduct gas - 99.96 - - - - - 0.04 - -

YES Coal

Stoker/SlopedGrate/Other 1 KYISPChemicals 0AA (Riley)

D/F Total Mass Sample #2 11/17/2009 2.30E-03 -6.07E+00 0

Coal: Sub-bituminous/Process coproduct gas - 99.96 - - - - - 0.04 - -

YES Coal

Stoker/SlopedGrate/Other 1 KYISPChemicals 0AA (Riley)

D/F Total Mass Sample #3 11/18/2009 2.10E-03 -6.17E+00 0

Coal: Sub-bituminous/Process coproduct gas - 99.96 - - - - - 0.04 - -

YES Coal

Stoker/SlopedGrate/Other 2 WINewPageBiron B24

D/F Total Mass Sample #1 9/24/2009 DLL 1.33E-02 -4.32E+00 1 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - - - - - -

YES Coal

Stoker/SlopedGrate/Other 2 WINewPageBiron B24

D/F Total Mass Sample #2 9/24/2009 DLL 1.38E-02 -4.28E+00 1 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - - - - - -

YES Coal

Stoker/SlopedGrate/Other 2 WINewPageBiron B24

D/F Total Mass Sample #3 9/24/2009 DLL 9.99E-03 -4.61E+00 1 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - - - - - -
Appendix C-11: Ranked Existing Unit Performance by Fuel

In top 

12%?

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common Pollutant_Name TestID

TestDate_co

mmon

NonDetect? ng/dscm @ 7% O2 ln (ng/dscm @ 7% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

YES Gas 1 1 NCCampLejeuneMCB

C-AS-4151-16 TEQ Dioxin/Furans Sample #1 no 3.73E-03 -5.59E+00 Natural gas - - - - - 

YES Gas 1 1 NCCampLejeuneMCB

C-AS-4151-16 TEQ Dioxin/Furans Sample #2 no 1.27E-03 -6.67E+00 Natural gas - - - - - 

YES Gas 1 1 NCCampLejeuneMCB

C-AS-4151-16 TEQ Dioxin/Furans Sample #3 no 2.70E-03 -5.92E+00 Natural gas - - - - - 

YES Gas 1 yes 1 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 TEQ Dioxin/Furans M23-1 no DLL 2.70E-03 -5.92E+00 Natural gas - - - - - 

YES Gas 1 yes 1 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 TEQ Dioxin/Furans M23-2 no DLL 2.33E-03 -6.06E+00 Natural gas - - - - - 

YES Gas 1 yes 1 CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 TEQ Dioxin/Furans M23-3 no DLL 2.70E-03 -5.91E+00 Natural gas - - - - - 

YES Gas 2 1 SCBMWManufacturingCo HB03 TEQ Dioxin/Furans Sample #1 no DLL 2.21E-03 -6.11E+00 Landfill Gas - - - - - 

YES Gas 2 1 SCBMWManufacturingCo HB03 TEQ Dioxin/Furans Sample #2 no DLL 3.80E-03 -5.57E+00 Landfill Gas - - - - - 

YES Gas 2 1 SCBMWManufacturingCo HB03 TEQ Dioxin/Furans Sample #3 no DLL 2.00E-03 -6.22E+00 Landfill Gas - - - - - 

YES Liquid 1 SCMilliken-Dewey D30 TEQ Dioxin/Furans Sample #1 no BDL 3.43E-06 -1.26E+01 Anhydrides Waste - - - - 100.00 

YES Liquid 1 SCMilliken-Dewey D30 TEQ Dioxin/Furans Sample #2 no BDL 2.88E-06 -1.28E+01 Anhydrides Waste - - - - 100.00 YES Liquid 1 SCMilliken-Dewey D30 TEQ Dioxin/Furans Sample #3 no BDL 2.67E-06 -1.28E+01 Anhydrides Waste - - - - 100.00 YES Liquid 2 CTElectric Boat EMU 17 TEQ Dioxin/Furans Sample #1 no 1.18E-03 -6.75E+00 No. 4 Fuel oil - - - - - 

YES Liquid 2 CTElectric Boat EMU 17 TEQ Dioxin/Furans Sample #2 no 1.08E-03 -6.83E+00 No. 4 Fuel oil - - - - - 

YES Liquid 2 CTElectric Boat EMU 17 TEQ Dioxin/Furans Sample #3 no 1.03E-03 -6.88E+00 No. 4 Fuel oil - - - - - 

YES Liquid 3

NYConEd59thStStationNewYork Boiler 118 TEQ Dioxin/Furans Sample #1 no DLL 1.28E-03 -6.66E+00 No. 6 Residual oil - - - - 100.00 

YES Liquid 3

NYConEd59thStStationNewYork Boiler 118 TEQ Dioxin/Furans Sample #2 no DLL 1.23E-03 -6.70E+00 No. 6 Residual oil - - - - 100.00 

YES Liquid 3

NYConEd59thStStationNewYork Boiler 118 TEQ Dioxin/Furans Sample #3 no DLL 7.90E-04 -7.14E+00 No. 6 Residual oil - - - - 100.00 
Appendix C-12: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect? ng/dscm @ 7% O2 ln (ng/dscm @ 7% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

yes Biomass

Dutch Oven/Susp. Burner 1 ORFlakeboardEugene Boiler-2

TEQ Dioxin/Furans M23-1 no DLL 9.27E-03 -4.68E+00

Natural gas/Wood: Unadulterated Lumber - - - 30.60 - 

 

yes Biomass

Dutch Oven/Susp. Burner 1 ORFlakeboardEugene Boiler-2

TEQ Dioxin/Furans M23-2 no DLL 6.42E-03 -5.05E+00

Natural gas/Wood: Unadulterated Lumber - - - 30.60 - 

 

yes Biomass

Dutch Oven/Susp. Burner 1 ORFlakeboardEugene Boiler-2

TEQ Dioxin/Furans M23-3 no DLL 1.29E-02 -4.35E+00

Natural gas/Wood: Unadulterated Lumber - - - 30.60 - 

 

yes Biomass FB 1 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

TEQ Dioxin/Furans Sample #1 no DLL 2.29E-03 -6.08E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 76.28 20.70 

 

yes Biomass FB 1 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

TEQ Dioxin/Furans Sample #2 no DLL 3.00E-03 -5.81E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 76.28 20.70 

 

yes Biomass FB 1 ORGeorgiaPacificWaunaMill

EU35 - Fluidized Bed Boiler

TEQ Dioxin/Furans Sample #3 no DLL 1.52E-03 -6.49E+00

Hog Fuel/Industrial Sludge/Natural gas - - - 76.28 20.70 

 

yes Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11Cu301

TEQ Dioxin/Furans Sample #1 no DLL 2.44E-03 -6.02E+00

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 

 

yes Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11Cu301

TEQ Dioxin/Furans Sample #2 no DLL 3.05E-03 -5.79E+00

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 

 

yes Biomass FB 2 ALIPCourtland

No. 3 Combination Boier / 11Cu301

TEQ Dioxin/Furans Sample #3 no DLL 4.32E-03 -5.44E+00

Industrial Sludge/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark - - 88.42 - 2.96 

 

yes Biomass FB 3 TNBowaterNewsprint

Bubbling Fluidized Bed Boiler

TEQ 

Dioxin/Furans Sample #1 no DLL 2.97E-03 -5.82E+00

Biomass/Tire Derived Fuel (TDF)/Wood: Bark - - 93.79 2.59 - 

 

yes Biomass FB 3 TNBowaterNewsprint

Bubbling Fluidized Bed Boiler

TEQ Dioxin/Furans Sample #2 no DLL 6.09E-03 -5.10E+00

Biomass/Tire Derived Fuel (TDF)/Wood: Bark - - 93.79 2.59 - 

 

yes Biomass FB 3 TNBowaterNewsprint

Bubbling Fluidized Bed Boiler

TEQ Dioxin/Furans Sample #3 no DLL 6.83E-03 -4.99E+00

Biomass/Tire Derived Fuel (TDF)/Wood: Bark - - 93.79 2.59 - 

 

yes Biomass FB 4 GATempleInlandRome WF

TEQ Dioxin/Furans Sample #1 no DLL 1.89E-02 -3.97E+00 Wood: Bark - - 100.00 - - 

 

yes Biomass FB 4 GATempleInlandRome WF

TEQ Dioxin/Furans Sample #2 no DLL 3.80E-03 -5.57E+00 Wood: Bark - - 100.00 - - 

 

yes Biomass FB 4 GATempleInlandRome WF

TEQ Dioxin/Furans Sample #3 no DLL 5.64E-03 -5.18E+00 Wood: Bark - - 100.00 - - 

 

yes Biomass Fuel Cell 1 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

TEQ Dioxin/Furans Sample #1 no DLL 2.45E-04 -8.31E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 1 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

TEQ Dioxin/Furans Sample #2 no 2.71E-04 -8.21E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 1 WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

TEQ Dioxin/Furans Sample #3 no DLL 2.09E-04 -8.47E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 2 MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

TEQ Dioxin/Furans Sample #1 no DLL 4.06E-03 -5.51E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 2 MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

TEQ Dioxin/Furans Sample #2 no DLL 2.78E-03 -5.89E+00 Hog Fuel - - - 100.00 - 

 
Appendix C-12: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect? ng/dscm @ 7% O2 ln (ng/dscm @ 7% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

yes Biomass Fuel Cell 2 MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

TEQ Dioxin/Furans Sample #3 no DLL 3.21E-03 -5.74E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 3

ORWeyerhaeuserCoWarrentonLumberMill 3-HFB

TEQ Dioxin/Furans Sample #2 no 4.46E-03 -5.41E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 4 ARWeyerhaeuserDierksMill SN-45

TEQ Dioxin/Furans Sample #1 no DLL 1.47E-02 -4.22E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 4 ARWeyerhaeuserDierksMill SN-45

TEQ Dioxin/Furans Sample #2 no DLL 2.88E-05 -1.05E+01 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 4 ARWeyerhaeuserDierksMill SN-45

TEQ Dioxin/Furans Sample #3 no DLL 1.07E-02 -4.54E+00 Hog Fuel - - - 100.00 - 

 

yes Biomass Fuel Cell 5 ARAnthonyForestProducts SN-12

TEQ Dioxin/Furans Sample #1 no DLL 1.48E-02 -4.21E+00

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - 

 

yes Biomass Fuel Cell 5 ARAnthonyForestProducts SN-12

TEQ Dioxin/Furans Sample #2 no DLL 5.51E-03 -5.20E+00

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - 

 

yes Biomass Fuel Cell 5 ARAnthonyForestProducts SN-12

TEQ Dioxin/Furans Sample #3 no DLL 1.07E-02 -4.54E+00

Wood: Bark/Wood: Unadulterated Lumber/Wood: Unadulterated Timber - - 100.00 - - 

 

yes Biomass

Stoker/SlopedGrate/Other 1 ARGBPMorrilton SN-04

TEQ Dioxin/Furans 1 no DLL 2.20E-05 -1.07E+01 /Wood: Bark/ - - 100.00 - - 

 

yes Biomass

Stoker/SlopedGrate/Other 1 ARGBPMorrilton SN-04

TEQ Dioxin/Furans 2 no 1.16E-05 -1.14E+01 /Wood: Bark/ - - 100.00 - - 

 

yes Biomass

Stoker/SlopedGrate/Other 1 ARGBPMorrilton SN-04

TEQ Dioxin/Furans 3 no DLL 1.20E-05 -1.13E+01 /Wood: Bark/ - - 100.00 - - 

 

yes Biomass

Stoker/SlopedGrate/Other 2 MEBoralexStratton Boiler #1

TEQ Dioxin/Furans Sample #1 no DLL 9.67E-04 -6.94E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

yes Biomass

Stoker/SlopedGrate/Other 2 MEBoralexStratton Boiler #1

TEQ Dioxin/Furans Sample #2 no 2.76E-03 -5.89E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

yes Biomass

Stoker/SlopedGrate/Other 2 MEBoralexStratton Boiler #1

TEQ Dioxin/Furans Sample #3 no DLL 1.14E-03 -6.78E+00

Wood: Bark/Wood: Unadulterated Timber - - 100.00 - - 

 

yes Coal FB 1 SCSonocoHartsville

Boiler Number 9

TEQ Dioxin/Furans 1 no DLL 6.15E-06 -1.20E+01 /Coal: Bituminous/ - 100.00 - - - 

 

yes Coal FB 1 SCSonocoHartsville

Boiler Number 9

TEQ Dioxin/Furans 2 no DLL 9.14E-06 -1.16E+01 /Coal: Bituminous/ - 100.00 - - - 

 

yes Coal FB 1 SCSonocoHartsville

Boiler Number 9

TEQ Dioxin/Furans 3 no DLL 1.19E-05 -1.13E+01 /Coal: Bituminous/ - 100.00 - - - 

 

yes Coal FB 2 INPurdueUniverisity Boiler 5

TEQ Dioxin/Furans Sample #1 no DLL 8.43E-04 -7.08E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal FB 2 INPurdueUniverisity Boiler 5

TEQ Dioxin/Furans Sample #2 no DLL 9.55E-04 -6.95E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal FB 2 INPurdueUniverisity Boiler 5

TEQ Dioxin/Furans Sample #3 no DLL 1.00E-03 -6.91E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal PC 1 GAGPCedarSprings

U500 - Power Boiler No 1

TEQ Dioxin/Furans Sample #1 no DLL 1.02E-03 -6.89E+00

Coal: Bituminous/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark
Appendix C-12: Ranked Existing Unit Performance by Fuel and Combustor Design

In top 

12%?

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect? ng/dscm @ 7% O2 ln (ng/dscm @ 7% O2) Fuel Coal %

Bagasse %

Wet Biomass %

Dry Biomass %

Heavy Liquid %

yes Coal PC 1 GAGPCedarSprings

U500 - Power Boiler No 1

TEQ Dioxin/Furans Sample #2 no DLL 9.76E-04 -6.93E+00

Coal: Bituminous/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark

yes Coal PC 1 GAGPCedarSprings

U500 - Power Boiler No 1

TEQ Dioxin/Furans Sample #3 no DLL 1.12E-03 -6.79E+00

Coal: Bituminous/Natural gas/Tire Derived Fuel (TDF)/Wood: Bark

yes Coal PC 2 WVPPGMartinsville

R011-Boiler 3

TEQ Dioxin/Furans Sample #1 no DLL 2.44E-03 -6.02E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal PC 2 WVPPGMartinsville

R011-Boiler 3

TEQ Dioxin/Furans Sample #2 no DLL 2.07E-03 -6.18E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal PC 2 WVPPGMartinsville

R011-Boiler 3

TEQ Dioxin/Furans Sample #3 no DLL 1.86E-03 -6.29E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal

Stoker/SlopedGrate/Other 1 WINewPageBiron B24

TEQ Dioxin/Furans Sample #1 no DLL 1.35E-03 -6.60E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

yes Coal

Stoker/SlopedGrate/Other 1 WINewPageBiron B24

TEQ Dioxin/Furans Sample #2 no DLL 1.78E-03 -6.33E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

yes Coal

Stoker/SlopedGrate/Other 1 WINewPageBiron B24

TEQ Dioxin/Furans Sample #3 no DLL 1.42E-03 -6.55E+00 Coal: Sub-bituminous/Wood: Bark - 97.04 2.96 - - 

 

yes Coal

Stoker/SlopedGrate/Other 2 ILAbbottAbbottPark Unit 5AP

TEQ Dioxin/Furans Sample #1 no DLL 2.16E-03 -6.14E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal

Stoker/SlopedGrate/Other 2 ILAbbottAbbottPark Unit 5AP

TEQ Dioxin/Furans Sample #2 no DLL 1.91E-03 -6.26E+00 Coal: Bituminous - 100.00 - - - 

 

yes Coal

Stoker/SlopedGrate/Other 2 ILAbbottAbbottPark Unit 5AP

TEQ Dioxin/Furans Sample #3 no DLL 2.32E-03 -6.07E+00 Coal: Bituminous - 100.00 - - - 

 
Appendix D-1: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Biomass

No. of sources = 192 192

No. in MACT floor = 24 24

Avge of top 12% = 6.06E-03 -5.69E+00

Std Deviation of top 12% = 7.79E-03 1.15E+00

Skewness = 4.03 -0.46

Kurtosis = 25.75 1.18

SE Skewness 0.17 0.17

Skewness Test non-normal normal

SE Kurtosis 0.35 0.35

Kurtosis Test non-normal non-normal

Number of test runs = 197 197

Number of test runs that contained non-detect 

values

2 2

Highest test run = 7.10E-02 -2.65E+00

99% t-statistic for UPL 2.35E+00 2.35E+00

99% UPL of top 12% (test runs) = 1.67E-02 1.62E-02

Coal

No. of sources = 366 366

No. in MACT floor = 44 44

Avge of top 12% = 7.24E-03 -5.66E+00

Std Deviation of top 12% = 1.11E-02 1.21E+00

Skewness = 3.08 0.05

Kurtosis = 9.98 0.33

SE Skewness 0.15 0.15

Skewness Test non-normal normal

SE Kurtosis 0.29 0.29

Kurtosis Test non-normal normal

Number of test runs = 279 279

Number of test runs that contained non-detect 

values

3 3

Highest test run = 6.40E-02 -2.75E+00

99% t-statistic for UPL 2.34E+00 2.34E+00

99% UPL of top 12% (test runs) = 2.23E-02 1.79E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-1: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Liquid

No. of sources = 91 91

No. in MACT floor = 11 11

Avge of top 12% = 1.40E-03 -6.77E+00

Std Deviation of top 12% = 8.09E-04 7.09E-01

Skewness = 1.06 -1.33

Kurtosis = 1.62 3.41

SE Skewness 0.39 0.39

Skewness Test non-normal normal

SE Kurtosis 0.78 0.78

Kurtosis Test non-normal non-normal

Number of test runs = 39 39

Number of test runs that contained non-detect 

values

1 1

Highest test run = 4.00E-03 -5.52E+00

99% t-statistic for UPL 2.43E+00 2.43E+00

99% UPL of top 12% (test runs) = 2.57E-03 3.23E-03

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 144 144

No. in MACT floor = 18 18

Avge of top 12% = 3.88E-03 -7.45E+00

Std Deviation of top 12% = 1.45E-02 1.48E+00

Skewness = 6.14 1.69

Kurtosis = 42.28 2.99

SE Skewness 0.30 0.30

Skewness Test non-normal non-normal

SE Kurtosis 0.60 0.60

Kurtosis Test non-normal non-normal

Number of test runs = 66 66

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.08E-01 -2.23E+00

99% t-statistic for UPL 2.39E+00 2.39E+00

99% UPL of top 12% (test runs) = 2.42E-02 4.67E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-1: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 9 9

No. in MACT floor = 2 2

Avge of top 12% = 4.70E-03 -7.84E+00

Std Deviation of top 12% = 6.45E-03 3.50E+00

Skewness = 1.00 -0.49

Kurtosis = -1.03 -1.70

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.53E-02 -4.18E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 1.72E-02 3.41E-01

Gas 2

No. of sources = 13 13

No. in MACT floor = 2 2

Avge of top 12% = 1.10E-02 -5.24E+00

Std Deviation of top 12% = 1.15E-02 1.45E+00

Skewness = 1.23 -0.61

Kurtosis = 0.71 -0.39

SE Skewness 0.43 0.43

Skewness Test non-normal normal

SE Kurtosis 0.85 0.85

Kurtosis Test normal normal

Number of test runs = 33 33

Number of test runs that contained non-detect 

values

0 0

Highest test run = 4.21E-02 -3.17E+00

99% t-statistic for UPL 2.45E+00 2.45E+00

99% UPL of top 12% (test runs) = 2.79E-02 4.50E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-2: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Biomass

No. of sources = 91 91

No. in MACT floor = 11 11

Avge of top 12% = 3.46E-07 -1.51E+01

Std Deviation of top 12% = 2.31E-07 7.04E-01

Skewness = 0.94 -0.27

Kurtosis = -0.27 -0.07

SE Skewness 0.34 0.34

Skewness Test non-normal normal

SE Kurtosis 0.67 0.67

Kurtosis Test normal normal

Number of test runs = 53 53

Number of test runs that contained non-detect 

values

30 30

Highest test run = 9.18E-07 -1.39E+01

99% t-statistic for UPL 2.40E+00 2.40E+00

99% UPL of top 12% (test runs) = 6.76E-07 7.52E-07

Coal

No. of sources = 285 285

No. in MACT floor = 35 35

Avge of top 12% = 5.95E-07 -1.49E+01

Std Deviation of top 12% = 7.76E-07 1.19E+00

Skewness = 3.17 -0.44

Kurtosis = 12.04 0.48

SE Skewness 0.19 0.19

Skewness Test non-normal normal

SE Kurtosis 0.39 0.39

Kurtosis Test non-normal normal

Number of test runs = 161 161

Number of test runs that contained non-detect 

values

60 60

Highest test run = 5.07E-06 -1.22E+01

99% t-statistic for UPL 2.35E+00 2.35E+00

99% UPL of top 12% (test runs) = 1.66E-06 1.64E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-2: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Liquid

No. of sources = 177 177

No. in MACT floor = 22 22

Avge of top 12% = 1.91E-06 -1.34E+01

Std Deviation of top 12% = 6.40E-07 8.59E-01

Skewness = -2.26 -2.68

Kurtosis = 3.28 5.94

SE Skewness 0.12 0.12

Skewness Test normal normal

SE Kurtosis 0.24 0.24

Kurtosis Test non-normal non-normal

Number of test runs = 400 400

Number of test runs that contained non-detect 

values

377 377

Highest test run = 2.25E-06 -1.30E+01

99% t-statistic for UPL 2.34E+00 2.34E+00

99% UPL of top 12% (test runs) = 2.78E-06 5.05E-06

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 14 14

No. in MACT floor = 2 2

Avge of top 12% = 1.07E-07 -1.61E+01

Std Deviation of top 12% = 3.73E-08 3.49E-01

Skewness = 0.64 -0.01

Kurtosis = -0.27 -0.12

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.65E-07 -1.56E+01

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.96E-07 2.34E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-2: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 7 7

No. in MACT floor = 1 1

Avge of top 12% = 3.32E-08 -1.74E+01

Std Deviation of top 12% = 2.65E-08 8.31E-01

Skewness = 1.29 0.38

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 6.28E-08 -1.66E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.84E-07 2.98E-06

Gas 2

No. of sources = 8 8

No. in MACT floor = 1 1

Avge of top 12% = 8.25E-08 -1.63E+01

Std Deviation of top 12% = 1.82E-08 2.13E-01

Skewness = 1.38 1.24

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.03E-07 -1.61E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.86E-07 2.73E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-3: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Biomass

No. of sources = 92 92

No. in MACT floor = 12 12

Avge of top 12% = 4.34E-03 -8.39E+00

Std Deviation of top 12% = 1.26E-02 2.29E+00

Skewness = 3.48 0.82

Kurtosis = 12.51 0.71

SE Skewness 0.34 0.34

Skewness Test non-normal non-normal

SE Kurtosis 0.68 0.68

Kurtosis Test non-normal normal

Number of test runs = 52 52

Number of test runs that contained non-detect 

values

17 17

Highest test run = 6.43E-02 -2.74E+00

99% t-statistic for UPL 2.40E+00 2.40E+00

99% UPL of top 12% (test runs) = 2.22E-02 6.00E-03

Coal

No. of sources = 318 318

No. in MACT floor = 39 39

Avge of top 12% = 4.23E-03 -7.08E+00

Std Deviation of top 12% = 1.89E-02 1.59E+00

Skewness = 6.98 0.02

Kurtosis = 47.84 1.25

SE Skewness 0.20 0.20

Skewness Test non-normal normal

SE Kurtosis 0.39 0.39

Kurtosis Test non-normal non-normal

Number of test runs = 157 157

Number of test runs that contained non-detect 

values

25 25

Highest test run = 1.40E-01 -1.97E+00

99% t-statistic for UPL 2.35E+00 2.35E+00

99% UPL of top 12% (test runs) = 3.02E-02 7.38E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-3: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Liquid

No. of sources = 190 190

No. in MACT floor = 23 23

Avge of top 12% = 2.59E-04 -8.34E+00

Std Deviation of top 12% = 4.97E-05 6.59E-01

Skewness = -1.31 -6.35

Kurtosis = 29.24 40.99

SE Skewness 0.10 0.10

Skewness Test normal normal

SE Kurtosis 0.21 0.21

Kurtosis Test non-normal non-normal

Number of test runs = 556 556

Number of test runs that contained non-detect 

values

535 535

Highest test run = 6.24E-04 -7.38E+00

99% t-statistic for UPL 2.33E+00 2.33E+00

99% UPL of top 12% (test runs) = 3.26E-04 5.82E-04

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 11 11

No. in MACT floor = 2 2

Avge of top 12% = 1.01E-04 -9.29E+00

Std Deviation of top 12% = 3.91E-05 5.02E-01

Skewness = -1.08 -1.39

Kurtosis = -0.72 0.79

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

5 5

Highest test run = 1.30E-04 -8.95E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.94E-04 3.04E-04

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-3: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 9 9

No. in MACT floor = 2 2

Avge of top 12% = 1.92E-04 -8.66E+00

Std Deviation of top 12% = 8.04E-05 5.32E-01

Skewness = -0.85 -0.90

Kurtosis = -1.63 -1.47

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

6 6

Highest test run = 2.54E-04 -8.28E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 3.48E-04 4.83E-04

Gas 2

No. of sources = 8 8

No. in MACT floor = 1 1

Avge of top 12% = 1.70E-06 -1.33E+01

Std Deviation of top 12% = 1.41E-07 8.25E-02

Skewness = 0.63 0.51

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.85E-06 -1.32E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 2.50E-06 2.71E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-4: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Liquid

No. of sources = 116 116

No. in MACT floor = 14 14

Avge of top 12% = 4.43E-01 -1.16E+00

Std Deviation of top 12% = 3.22E-01 9.31E-01

Skewness = 0.61 -0.60

Kurtosis = -0.64 -0.50

SE Skewness 0.39 0.39

Skewness Test normal normal

SE Kurtosis 0.77 0.77

Kurtosis Test normal normal

Number of test runs = 40 40

Number of test runs that contained non-detect 

values

11 11

Highest test run = 1.22E+00 1.95E-01

99% t-statistic for UPL 2.43E+00 2.43E+00

99% UPL of top 12% (test runs) = 9.11E-01 1.22E+00

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 754 754

No. in MACT floor = 91 91

Avge of top 12% = 1.45E+00 -1.95E+00

Std Deviation of top 12% = 1.16E+01 1.32E+00

Skewness = 13.74 2.08

Kurtosis = 207.35 6.81

SE Skewness 0.14 0.14

Skewness Test non-normal non-normal

SE Kurtosis 0.28 0.28

Kurtosis Test non-normal non-normal

Number of test runs = 299 299

Number of test runs that contained non-detect 

values

120 120

Highest test run = 1.84E+02 5.21E+00

99% t-statistic for UPL 2.34E+00 2.34E+00

99% UPL of top 12% (test runs) = 1.72E+01 8.55E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-4: UPL Calculations for Existing Units

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 15 15

No. in MACT floor = 2 2

Avge of top 12% = 3.79E-01 -1.27E+00

Std Deviation of top 12% = 2.99E-01 8.79E-01

Skewness = 0.81 -0.01

Kurtosis = -0.51 -1.88

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 8.59E-01 -1.52E-01

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.09E+00 2.28E+00

Gas 2

No. of sources = 75 75

No. in MACT floor = 9 9

Avge of top 12% = 7.37E-02 -2.89E+00

Std Deviation of top 12% = 4.04E-02 8.91E-01

Skewness = -0.77 -0.90

Kurtosis = -1.43 -1.13

SE Skewness 0.45 0.45

Skewness Test normal normal

SE Kurtosis 0.89 0.89

Kurtosis Test normal normal

Number of test runs = 30 30

Number of test runs that contained non-detect 

values

2 2

Highest test run = 1.10E-01 -2.21E+00

99% t-statistic for UPL 2.46E+00 2.46E+00

99% UPL of top 12% (test runs) = 1.34E-01 2.10E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-4: UPL Calculations for Existing Units

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Dutch Oven

No. of sources = 17 17

No. in MACT floor = 3 3

Avge of top 12% = 3.62E+02 5.51E+00

Std Deviation of top 12% = 3.32E+02 9.79E-01

Skewness = 2.34 -0.92

Kurtosis = 6.84 1.59

SE Skewness 0.35 0.35

Skewness Test non-normal normal

SE Kurtosis 0.71 0.71

Kurtosis Test non-normal non-normal

Number of test runs = 48 48

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.72E+03 7.45E+00

99% t-statistic for UPL 2.41E+00 2.41E+00

99% UPL of top 12% (test runs) = 8.38E+02 1.01E+03

Biomass - Fluidized Bed

No. of sources = 7 7

No. in MACT floor = 5 5

Avge of top 12% = 9.71E+01 4.27E+00

Std Deviation of top 12% = 8.34E+01 8.08E-01

Skewness = 1.83 0.14

Kurtosis = 3.56 -0.83

SE Skewness 0.50 0.50

Skewness Test non-normal normal

SE Kurtosis 1.00 1.00

Kurtosis Test non-normal normal

Number of test runs = 24 24

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.48E+02 5.85E+00

99% t-statistic for UPL 2.50E+00 2.50E+00

99% UPL of top 12% (test runs) = 2.25E+02 2.45E+02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-4: UPL Calculations for Existing Units

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Fuel Cell

No. of sources = 16 16

No. in MACT floor = 5 5

Avge of top 12% = 1.30E+02 4.69E+00

Std Deviation of top 12% = 7.82E+01 6.03E-01

Skewness = 0.86 0.12

Kurtosis = -0.26 -1.17

SE Skewness 0.40 0.40

Skewness Test non-normal normal

SE Kurtosis 0.79 0.79

Kurtosis Test normal normal

Number of test runs = 38 38

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.10E+02 5.74E+00

99% t-statistic for UPL 2.43E+00 2.43E+00

99% UPL of top 12% (test runs) = 2.44E+02 2.62E+02

Biomass - Stoker

No. of sources = 119 119

No. in MACT floor = 15 15

Avge of top 12% = 2.03E+02 4.57E+00

Std Deviation of top 12% = 4.08E+02 1.23E+00

Skewness = 5.12 -0.67

Kurtosis = 28.47 2.92

SE Skewness 0.30 0.30

Skewness Test non-normal normal

SE Kurtosis 0.60 0.60

Kurtosis Test non-normal non-normal

Number of test runs = 67 67

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.78E+03 7.93E+00

99% t-statistic for UPL 2.38E+00 2.38E+00

99% UPL of top 12% (test runs) = 7.77E+02 5.51E+02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-4: UPL Calculations for Existing Units

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Coal - FB

No. of sources = 17 17

No. in MACT floor = 3 3

Avge of top 12% = 1.25E+01 2.43E+00

Std Deviation of top 12% = 4.64E+00 5.41E-01

Skewness = -1.15 -1.92

Kurtosis = 0.63 3.72

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal non-normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.68E+01 2.82E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 2.14E+01 3.21E+01

Coal - PC

No. of sources = 41 41

No. in MACT floor = 5 5

Avge of top 12% = 1.92E+01 -2.38E-01

Std Deviation of top 12% = 3.29E+01 3.04E+00

Skewness = 1.24 0.59

Kurtosis = -0.50 -1.34

SE Skewness 0.50 0.50

Skewness Test non-normal normal

SE Kurtosis 1.00 1.00

Kurtosis Test normal normal

Number of test runs = 24 24

Number of test runs that contained non-detect 

values

0 0

Highest test run = 7.79E+01 4.36E+00

99% t-statistic for UPL 2.50E+00 2.50E+00

99% UPL of top 12% (test runs) = 6.97E+01 8.28E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-4: UPL Calculations for Existing Units

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Coal - Stoker

No. of sources = 61 61

No. in MACT floor = 8 8

Avge of top 12% = 2.14E+01 2.90E+00

Std Deviation of top 12% = 1.10E+01 6.43E-01

Skewness = 1.04 -1.26

Kurtosis = 3.21 1.67

SE Skewness 0.50 0.50

Skewness Test non-normal normal

SE Kurtosis 1.00 1.00

Kurtosis Test non-normal normal

Number of test runs = 24 24

Number of test runs that contained non-detect 

values

0 0

Highest test run = 5.57E+01 4.02E+00

99% t-statistic for UPL 2.50E+00 2.50E+00

99% UPL of top 12% (test runs) = 3.82E+01 4.88E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-5: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Liquid

No. of sources = 17 17

No. in MACT floor = 3 3

Avge of top 12% = 7.33E-04 -8.79E+00

Std Deviation of top 12% = 5.65E-04 2.95E+00

Skewness = -0.64 -0.85

Kurtosis = -1.78 -1.71

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

6 6

Highest test run = 1.28E-03 -6.66E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 1.82E-03 4.54E-02

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 8 8

No. in MACT floor = 1 1

Avge of top 12% = 2.57E-03 -6.06E+00

Std Deviation of top 12% = 1.23E-03 5.52E-01

Skewness = -0.47 -1.08

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.73E-03 -5.59E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 9.59E-03 5.41E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-5: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 7 7

No. in MACT floor = 1 1

Avge of top 12% = 2.58E-03 -5.96E+00

Std Deviation of top 12% = 2.15E-04 8.58E-02

Skewness = -1.73 -1.73

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.70E-03 -5.91E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 3.80E-03 4.19E-03

Gas 2

No. of sources = 5 5

No. in MACT floor = 1 1

Avge of top 12% = 2.67E-03 -5.97E+00

Std Deviation of top 12% = 9.86E-04 3.46E-01

Skewness = 1.64 1.56

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 3.80E-03 -5.57E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 8.28E-03 1.83E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-5: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Dutch Oven

No. of sources = 3 3

No. in MACT floor = 1 1

Avge of top 12% = 9.52E-03 -4.69E+00

Std Deviation of top 12% = 3.23E-03 3.48E-01

Skewness = 0.34 -0.17

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.29E-02 -4.35E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 2.79E-02 6.63E-02

Biomass - Fluidized Bed

No. of sources = 6 6

No. in MACT floor = 5 5

Avge of top 12% = 5.07E-03 -5.52E+00

Std Deviation of top 12% = 4.65E-03 6.56E-01

Skewness = 2.75 1.06

Kurtosis = 8.40 1.91

SE Skewness 0.71 0.71

Skewness Test non-normal normal

SE Kurtosis 1.41 1.41

Kurtosis Test non-normal normal

Distribution = L N

Number of test runs = 12 12

Number of test runs that contained non-detect 

values

12 12

Highest test run = 1.89E-02 -3.97E+00

99% t-statistic for UPL 2.72E+00 2.72E+00

99% t-statistic for UL 2.68E+00 2.68E+00

99% UPL of top 12% (test runs) = 1.32E-02 1.27E-02

99% UL of top 12% (test runs) = 1.75E-02 2.32E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-5: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Fuel Cell

No. of sources = 7 7

No. in MACT floor = 5 5

Avge of top 12% = 5.52E-03 -6.21E+00

Std Deviation of top 12% = 5.43E-03 1.99E+00

Skewness = 0.75 -0.98

Kurtosis = -0.86 -0.11

SE Skewness 0.68 0.68

Skewness Test normal normal

SE Kurtosis 1.36 1.36

Kurtosis Test normal normal

Number of test runs = 13 13

Number of test runs that contained non-detect 

values

11 11

Highest test run = 1.48E-02 -4.21E+00

99% t-statistic for UPL 2.68E+00 2.68E+00

99% UPL of top 12% (test runs) = 1.48E-02 6.15E-02

Biomass - Stoker

No. of sources = 16 16

No. in MACT floor = 2 2

Avge of top 12% = 8.19E-04 -8.84E+00

Std Deviation of top 12% = 1.08E-03 2.56E+00

Skewness = 1.38 0.05

Kurtosis = 1.72 -3.00

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

4 4

Highest test run = 2.76E-03 -5.89E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 3.39E-03 6.35E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-5: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Coal - FB

No. of sources = 12 12

No. in MACT floor = 2 2

Avge of top 12% = 4.71E-04 -9.31E+00

Std Deviation of top 12% = 5.09E-04 2.57E+00

Skewness = 0.04 -0.03

Kurtosis = -3.22 -3.25

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

6 6

Highest test run = 1.00E-03 -6.91E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.68E-03 4.04E-02

Coal - PC

No. of sources = 10 10

No. in MACT floor = 2 2

Avge of top 12% = 1.58E-03 -6.52E+00

Std Deviation of top 12% = 6.25E-04 4.02E-01

Skewness = 0.34 0.14

Kurtosis = -2.16 -2.64

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

6 6

Highest test run = 2.44E-03 -6.02E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 3.07E-03 3.85E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-5: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Coal - Stoker

No. of sources = 14 14

No. in MACT floor = 2 2

Avge of top 12% = 1.82E-03 -6.33E+00

Std Deviation of top 12% = 3.87E-04 2.18E-01

Skewness = -0.05 -0.27

Kurtosis = -1.65 -1.71

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

6 6

Highest test run = 2.32E-03 -6.07E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 2.74E-03 3.00E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-6: UPL Calculations for Existing Units

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Liquid

No. of sources = 17 17

No. in MACT floor = 3 3

Avge of top 12% = 3.55E-03 -7.27E+00

Std Deviation of top 12% = 4.09E-03 2.69E+00

Skewness = 0.78 -0.59

Kurtosis = -1.48 -1.72

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

6 6

Highest test run = 9.90E-03 -4.62E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 1.15E-02 1.26E-01

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 8 8

No. in MACT floor = 1 1

Avge of top 12% = 1.21E-01 -2.19E+00

Std Deviation of top 12% = 5.12E-02 5.12E-01

Skewness = -1.73 -1.73

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.51E-01 -1.89E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 4.12E-01 2.06E+00

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-6: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 7 7

No. in MACT floor = 1 1

Avge of top 12% = 1.27E-02 -4.37E+00

Std Deviation of top 12% = 2.12E-18 0.00E+00

Skewness = -2.45 #DIV/0!

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal #DIV/0!

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.27E-02 -4.37E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.27E-02 1.27E-02

Gas 2

No. of sources = 5 5

No. in MACT floor = 1 1

Avge of top 12% = 4.50E-02 -3.18E+00

Std Deviation of top 12% = 2.03E-02 5.02E-01

Skewness = -0.30 -0.92

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 6.46E-02 -2.74E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.60E-01 7.23E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-6: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Dutch Oven

No. of sources = 3 3

No. in MACT floor = 1 1

Avge of top 12% = 1.63E-01 -1.88E+00

Std Deviation of top 12% = 6.36E-02 4.40E-01

Skewness = -0.88 -1.26

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.19E-01 -1.52E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 5.24E-01 1.87E+00

Biomass - Fluidized Bed

No. of sources = 6 6

No. in MACT floor = 5 5

Avge of top 12% = 2.14E-01 -2.20E+00

Std Deviation of top 12% = 3.08E-01 1.16E+00

Skewness = 2.96 0.37

Kurtosis = 9.69 -0.47

SE Skewness 0.63 0.63

Skewness Test non-normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test non-normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 1.24E+00 2.13E-01

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 7.26E-01 7.65E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-6: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Fuel Cell

No. of sources = 7 7

No. in MACT floor = 5 5

Avge of top 12% = 2.04E-01 -2.63E+00

Std Deviation of top 12% = 2.46E-01 2.01E+00

Skewness = 1.66 -1.42

Kurtosis = 2.78 2.94

SE Skewness 0.68 0.68

Skewness Test non-normal normal

SE Kurtosis 1.36 1.36

Kurtosis Test non-normal non-normal

Number of test runs = 13 13

Number of test runs that contained non-detect 

values

11 11

Highest test run = 8.40E-01 -1.75E-01

99% t-statistic for UPL 2.68E+00 2.68E+00

99% UPL of top 12% (test runs) = 6.26E-01 2.30E+00

Biomass - Stoker

No. of sources = 16 16

No. in MACT floor = 2 2

Avge of top 12% = 3.46E-02 -3.42E+00

Std Deviation of top 12% = 1.11E-02 3.63E-01

Skewness = -0.69 -0.85

Kurtosis = -1.71 -1.57

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

6 6

Highest test run = 4.61E-02 -3.08E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 6.09E-02 7.80E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-6: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Coal - FB

No. of sources = 12 12

No. in MACT floor = 2 2

Avge of top 12% = 9.23E-03 -5.39E+00

Std Deviation of top 12% = 1.22E-02 1.25E+00

Skewness = 1.68 1.05

Kurtosis = 2.25 -1.00

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

6 6

Highest test run = 3.18E-02 -3.45E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 3.83E-02 8.88E-02

Coal - PC

No. of sources = 10 10

No. in MACT floor = 2 2

Avge of top 12% = 1.86E-02 -4.00E+00

Std Deviation of top 12% = 3.90E-03 2.05E-01

Skewness = 0.79 0.33

Kurtosis = 1.15 0.27

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

6 6

Highest test run = 2.52E-02 -3.68E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 2.79E-02 2.98E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix D-6: UPL Calculations for Existing Units

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Coal - Stoker

No. of sources = 14 14

No. in MACT floor = 2 2

Avge of top 12% = 7.45E-03 -5.20E+00

Std Deviation of top 12% = 5.55E-03 8.90E-01

Skewness = 0.19 -0.03

Kurtosis = -2.80 -2.93

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.38E-02 -4.28E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 2.07E-02 4.59E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix E-1: Specific Data Excluded From Floor Analysis

Classification

10% Fuel 

Cat Data Source SourceTab FacilityID CombustorID TestID TestDate

Pollutant_Na

me Emission Value

Emission 

Units Not

Boiler Gas 1 ICR Phase I

PM and Metals (3)

CAConocoPhilipsLosAng D687 - Boiler 8

Sample #1 6/17/1998

Mercury (Hg) 4.073E-08 lb/MMBtu

Test report notes this value detection limit values. This for baseline or floor analyse

Boiler Gas 1 ICR Phase I

PM and Metals (3)

CAConocoPhilipsLosAng D687 - Boiler 8

Sample #2 6/18/1998

Mercury (Hg) 5.753E-09 lb/MMBtu

Test report notes this value detection limit values. This for baseline or floor analyse

Boiler Gas 1 ICR Phase I

PM and Metals (3)

CAConocoPhilipsLosAng D687 - Boiler 8

Sample #3 6/19/1998

Mercury (Hg) 5.754E-09 lb/MMBtu

Test report notes this value detection limit values. This for baseline or floor analyse

Boiler Gas 1 ICR Phase I

PMandMetals(75F1)020590

CAExxonMobilTorrance 75F-1 Sample #1 2/5/1990 Mercury (Hg) 0.0000817 lb/MMBtu

This test is from 1990 and of magnitude higher than othe same year at the same is available. Data was not u

Process Heater Gas 1

ICR Phase II - Templates Metals

CTCytecWallingford 150 Furnace

Sample #1 9/2/2009

Mercury (Hg) 0.000293 lb/MMBtu

ERT data does not match vreport. However, report listdetection limits are listed hhigh, so values were not usanalyses. 

Process Heater Gas 1

ICR Phase II - Templates Metals

CTCytecWallingford 150 Furnace

Sample #2 9/2/2009

Mercury (Hg) 0.000293 lb/MMBtu

ERT data does not match vreport. However, report listdetection limits are listed hhigh, so values were not usanalyses. 

Process Heater Gas 1

ICR Phase II - Templates Metals

CTCytecWallingford 150 Furnace

Sample #3 9/3/2009

Mercury (Hg) 0.000293 lb/MMBtu

ERT data does not match vreport. However, report listdetection limits are listed hhigh, so values were not usanalyses. 

Boiler

Dry Biomass

ICR Phase II - Templates

PM (filter) -

Duct

WAGraysHarborPaper No. 6 Boiler (EU2)

Sample #1 8/12/2009

Particulate Matter (PM) filterable 0.000482024 lb/MMBtu

Cannot use OTM 27 data oused in floor analyses. 

Boiler

Dry Biomass

ICR Phase II - Templates

PM (filter) -

Duct

WAGraysHarborPaper No. 6 Boiler (EU2)

Sample #2 8/13/2009

Particulate Matter (PM) filterable 0.001005905 lb/MMBtu

Cannot use OTM 27 data oused in floor analyses. 

Boiler

Dry Biomass

ICR Phase II - Templates

PM (filter) -

Duct

WAGraysHarborPaper No. 6 Boiler (EU2)

Sample #3 8/13/2009

Particulate Matter (PM) filterable 0.000503881 lb/MMBtu

Cannot use OTM 27 data oused in floor analyses. 

Boiler

Dry Biomass

ICR Phase II - Templates

PM (filter) -

Stack

WAGraysHarborPaper No. 6 Boiler (EU2)

Sample #1 8/12/2009

Particulate Matter (PM) filterable 0.000482024 lb/MMBtu

Cannot use OTM 27 data oused in floor analyses. 

Boiler

Dry Biomass

ICR Phase II - Templates

PM (filter) -

Stack

WAGraysHarborPaper No. 6 Boiler (EU2)

Sample #2 8/13/2009

Particulate Matter (PM) filterable 0.001005905 lb/MMBtu

Cannot use OTM 27 data oused in floor analyses. 
Appendix E-1: Specific Data Excluded From Floor Analysis

Classification

10% Fuel 

Cat Data Source SourceTab FacilityID CombustorID TestID TestDate

Pollutant_Na

me Emission Value

Emission 

Units Not

Boiler

Dry Biomass

ICR Phase II - Templates

PM (filter) -

Stack

WAGraysHarborPaper No. 6 Boiler (EU2)

Sample #3 8/13/2009

Particulate Matter (PM) filterable 0.000503881 lb/MMBtu

Cannot use OTM 27 data oused in floor analyses. 

Boiler Gas 1 ICR Phase I

PM and Metals (030B12)

TXEastmanChemLongview UD030B12

Sample #1 8/28/1981

Particulate Matter (PM) filterable 0.05 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 1 ICR Phase I

PM and Metals (030B12)

TXEastmanChemLongview UD030B12

Sample #2 8/28/1981

Particulate Matter (PM) filterable 0.057 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 1 ICR Phase I

PM and Metals (030B12)

TXEastmanChemLongview UD030B12

Sample #3 8/28/1981

Particulate Matter (PM) filterable 0.035 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 1 ICR Phase I

PM and Metals (030B12-2)

TXEastmanChemLongview UD030B12

Sample #1 6/13/1978

Particulate Matter (PM) filterable 0.044057971 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 1 ICR Phase I

PM and Metals (030B12-2)

TXEastmanChemLongview UD030B12

Sample #2 6/13/1978

Particulate Matter (PM) filterable 0.079130435 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 1 ICR Phase I

PM and Metals (030B12-2)

TXEastmanChemLongview UD030B12

Sample #3 6/13/1978

Particulate Matter (PM) filterable 0.093333333 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 2 ICR Phase I

PM and Metals

TXEastmanChemLongview OL225B1A

Sample #1 4/19/1984

Particulate Matter (PM) filterable 0.018 lb/MMBtu

Unit has not burned liquid f20 years. This test is not inoperations. 

Boiler Gas 2 ICR Phase I

PM and Metals

TXEastmanChemLongview OL225B1A

Sample #2 4/19/1984

Particulate Matter (PM) filterable 0.016 lb/MMBtu

Unit has not burned liquid f20 years. This test is not inoperations. 

Boiler Gas 2 ICR Phase I

PM and Metals

TXEastmanChemLongview OL225B1A

Sample #3 4/19/1984

Particulate Matter (PM) filterable 0.013 lb/MMBtu

Unit has not burned liquid f20 years. This test is not inoperations. 

Boiler Gas 1 ICR Phase I

PM and Metals (030B12-2)

TXEastmanChemLongview UD030B12

Sample #1 6/13/1978

Particulate Matter (total, including condensibles) 0.076231884 lb/MMBtu

Not reflective of current condata point for baseline dete
Appendix E-1: Specific Data Excluded From Floor Analysis

Classification

10% Fuel 

Cat Data Source SourceTab FacilityID CombustorID TestID TestDate

Pollutant_Na

me Emission Value

Emission 

Units Not

Boiler Gas 1 ICR Phase I

PM and Metals (030B12-2)

TXEastmanChemLongview UD030B12

Sample #2 6/13/1978

Particulate Matter (total, including condensibles) 0.096811594 lb/MMBtu

Not reflective of current condata point for baseline dete

Boiler Gas 1 ICR Phase I

PM and Metals (030B12-2)

TXEastmanChemLongview UD030B12

Sample #3 6/13/1978

Particulate Matter (total, including condensibles) 0.792753623 lb/MMBtu

Not reflective of current condata point for baseline dete

Process Heater Gas 1

ICR Phase II - Test Report

Phase II D/F From Test Report

WICharterSteel P31

Sample #2 9/14/2009

Total Dioxins/Furans 650

ng/dscm @ 7% O2

Not used for baseline/MACvalue is a TEQ value. 
Appendix F-1 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Biomass

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.16E-03 -6.89E+00

Std Deviation of top performer = 2.56E-03 1.35E+00

Skewness = 1.17 0.31

Kurtosis = -0.07 -1.43

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

0 0

Highest test run = 7.10E-03 -4.95E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top performer (test runs) = 7.11E-03 1.38E-02

Coal

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 3.96E-04 -7.98E+00

Std Deviation of top performer = 2.24E-04 5.98E-01

Skewness = 0.33 0.12

Kurtosis = -2.23 -2.95

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 7.06E-04 -7.26E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 9.28E-04 1.42E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-1 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Liquid

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 5.11E-04 -7.62E+00

Std Deviation of top performer = 1.80E-04 3.29E-01

Skewness = 1.73 1.72

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

1 1

Highest test run = 7.19E-04 -7.24E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.54E-03 3.19E-03

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.33E-04 -8.98E+00

Std Deviation of top performer = 5.77E-05 4.00E-01

Skewness = 1.73 1.73

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.00E-04 -8.52E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 4.62E-04 1.23E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-1 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 6.54E-03 -8.31E+00

Std Deviation of top performer = 7.37E-03 4.34E+00

Skewness = 0.22 0.00

Kurtosis = -2.79 -3.31

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.53E-02 -4.18E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 2.41E-02 7.45E+00

Gas 2

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 4.20E-04 -7.99E+00

Std Deviation of top performer = 3.48E-04 7.65E-01

Skewness = 1.72 1.68

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 8.21E-04 -7.10E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.40E-03 2.64E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-2 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Biomass

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 9.73E-08 -1.62E+01

Std Deviation of top performer = 1.55E-08 1.54E-01

Skewness = 1.55 1.49

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.15E-07 -1.60E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.86E-07 2.32E-07

Coal

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.18E-07 -1.67E+01

Std Deviation of top performer = 1.40E-07 1.35E+00

Skewness = 1.38 -0.03

Kurtosis = 0.37 -0.89

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

4 4

Highest test run = 3.77E-07 -1.48E+01

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top performer (test runs) = 3.89E-07 7.90E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-2 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Liquid

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 5.87E-08 -1.67E+01

Std Deviation of top performer = 3.31E-08 5.25E-01

Skewness = 1.63 1.48

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 9.66E-08 -1.62E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.47E-07 1.05E-06

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 9.35E-08 -1.62E+01

Std Deviation of top performer = 5.21E-09 5.50E-02

Skewness = 1.42 1.40

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 9.94E-08 -1.61E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.23E-07 1.28E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-2 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 3.32E-08 -1.74E+01

Std Deviation of top performer = 2.65E-08 8.31E-01

Skewness = 1.29 0.38

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 6.28E-08 -1.66E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.84E-07 2.98E-06

Gas 2

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 8.25E-08 -1.63E+01

Std Deviation of top performer = 1.82E-08 2.13E-01

Skewness = 1.38 1.24

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.03E-07 -1.61E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.86E-07 2.73E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-3 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Biomass

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 7.85E-04 -9.52E+00

Std Deviation of top performer = 9.58E-04 3.29E+00

Skewness = 0.64 0.04

Kurtosis = -1.96 -3.23

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.10E-03 -6.17E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 3.07E-03 1.82E-01

Coal

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 3.85E-05 -1.02E+01

Std Deviation of top performer = 2.39E-06 6.32E-02

Skewness = -1.63 -1.64

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 4.02E-05 -1.01E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 5.21E-05 5.51E-05

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-3 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Liquid

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 3.99E-04 -8.02E+00

Std Deviation of top performer = 2.44E-04 7.18E-01

Skewness = -0.05 -0.23

Kurtosis = -3.17 -2.58

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

3 3

Highest test run = 6.24E-04 -7.38E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 9.80E-04 1.81E-03

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 7.26E-05 -9.63E+00

Std Deviation of top performer = 3.82E-05 5.44E-01

Skewness = 0.80 0.04

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

2 2

Highest test run = 1.14E-04 -9.08E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.90E-04 1.45E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-3 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 8.59E-05 -9.37E+00

Std Deviation of top performer = 1.13E-05 1.30E-01

Skewness = 0.78 0.62

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 9.81E-05 -9.23E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.50E-04 1.79E-04

Gas 2

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.70E-06 -1.33E+01

Std Deviation of top performer = 1.41E-07 8.25E-02

Skewness = 0.63 0.51

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.85E-06 -1.32E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.50E-06 2.71E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-4 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Liquid

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.25E-01 -2.08E+00

Std Deviation of top performer = 0.00E+00 0.00E+00

Skewness = #DIV/0! #DIV/0!

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test #DIV/0! #DIV/0!

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.25E-01 -2.08E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.25E-01 1.25E-01

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 5.08E+00 -7.35E-01

Std Deviation of top performer = 8.37E+00 2.87E+00

Skewness = 1.64 0.22

Kurtosis = 1.99 -1.07

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.04E+01 3.02E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 2.50E+01 4.47E+02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-4 : UPL Calculations for New Sources

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 5.03E-01 -8.65E-01

Std Deviation of top performer = 2.95E-01 7.51E-01

Skewness = 0.01 -1.19

Kurtosis = 0.54 1.83

SE Skewness 1.22 1.22

Skewness Test normal normal

SE Kurtosis 2.45 2.45

Kurtosis Test normal normal

Number of test runs = 4 4

Number of test runs that contained non-detect 

values

0 0

Highest test run = 8.59E-01 -1.52E-01

99% t-statistic for UPL 4.54E+00 4.54E+00

99% UPL of top performer (test runs) = 1.53E+00 5.70E+00

Gas 2

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.29E-02 -4.35E+00

Std Deviation of top performer = 1.90E-18 0.00E+00

Skewness = 1.37 #DIV/0!

Kurtosis = -3.33 #DIV/0!

SE Skewness 1.00 1.00

Skewness Test normal #DIV/0!

SE Kurtosis 2.00 2.00

Kurtosis Test normal #DIV/0!

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.29E-02 -4.35E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 1.29E-02 1.29E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-4 : UPL Calculations for New Sources

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Dutch Oven

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 3.52E+02 5.52E+00

Std Deviation of top performer = 2.83E+02 9.78E-01

Skewness = 1.95 -1.29

Kurtosis = 5.37 2.41

SE Skewness 0.41 0.41

Skewness Test non-normal normal

SE Kurtosis 0.82 0.82

Kurtosis Test non-normal non-normal

Number of test runs = 36 36

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.45E+03 7.28E+00

99% t-statistic for UPL 2.44E+00 2.44E+00

99% UPL of top performer (test runs) = 7.66E+02 1.05E+03

Biomass - Fluidized Bed

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.58E+01 3.24E+00

Std Deviation of top performer = 3.51E+00 1.39E-01

Skewness = -0.19 -0.33

Kurtosis = -1.51 -1.59

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.03E+01 3.41E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 3.42E+01 3.56E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-4 : UPL Calculations for New Sources

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Fuel Cell

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.10E+02 4.53E+00

Std Deviation of top performer = 7.13E+01 6.15E-01

Skewness = 1.03 0.64

Kurtosis = -0.32 -1.75

SE Skewness 0.93 0.93

Skewness Test normal normal

SE Kurtosis 1.85 1.85

Kurtosis Test normal normal

Number of test runs = 7 7

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.33E+02 5.45E+00

99% t-statistic for UPL 3.14E+00 3.14E+00

99% UPL of top performer (test runs) = 2.64E+02 3.51E+02

Biomass - Stoker

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 9.20E+02 4.32E+00

Std Deviation of top performer = 1.18E+03 3.43E+00

Skewness = 0.93 -0.03

Kurtosis = -0.83 -2.92

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.78E+03 7.93E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top performer (test runs) = 3.73E+03 2.64E+05

Coal - FB

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 8.26E+00 1.94E+00

Std Deviation of top performer = 5.55E+00 7.47E-01

Skewness = 0.69 -0.36

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.42E+01 2.65E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 3.99E+01 4.87E+02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-4 : UPL Calculations for New Sources

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Coal - PC

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.50E+01 -4.81E-01

Std Deviation of top performer = 3.75E+01 3.60E+00

Skewness = 0.87 0.86

Kurtosis = -1.68 -1.71

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

0 0

Highest test run = 7.79E+01 4.36E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top performer (test runs) = 9.75E+01 6.44E+02

Coal - Stoker

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 4.29E+00 1.45E+00

Std Deviation of top performer = 3.93E-01 9.24E-02

Skewness = -0.34 -0.47

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 4.67E+00 1.54E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 6.53E+00 7.24E+00

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-5 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Liquid 14 16

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.09E-03 -6.82E+00

Std Deviation of top performer = 7.48E-05 6.78E-02

Skewness = 0.94 0.86

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.18E-03 -6.75E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.52E-03 1.61E-03

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.57E-03 -6.06E+00

Std Deviation of top performer = 1.23E-03 5.52E-01

Skewness = -0.47 -1.08

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.73E-03 -5.59E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 9.59E-03 5.41E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-5 : UPL Calculations for New Sources

Parameters

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.58E-03 -5.96E+00

Std Deviation of top performer = 2.15E-04 8.58E-02

Skewness = -1.73 -1.73

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.70E-03 -5.91E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 3.80E-03 4.19E-03

Gas 2

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.67E-03 -5.97E+00

Std Deviation of top performer = 9.86E-04 3.46E-01

Skewness = 1.64 1.56

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 3.80E-03 -5.57E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 8.28E-03 1.83E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-5 : UPL Calculations for New Sources

Parameters

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Dutch Oven

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 9.52E-03 -4.69E+00

Std Deviation of top performer = 3.23E-03 3.48E-01

Skewness = 0.34 -0.17

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.29E-02 -4.35E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.79E-02 6.63E-02

Biomass - Fluidized Bed

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.27E-03 -6.13E+00

Std Deviation of top performer = 7.41E-04 3.42E-01

Skewness = -0.10 -0.58

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 3.00E-03 -5.81E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 6.48E-03 1.53E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-5 : UPL Calculations for New Sources

Parameters

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Fuel Cell

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.42E-04 -8.33E+00

Std Deviation of top performer = 3.09E-05 1.30E-01

Skewness = -0.45 -0.62

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

2 2

Highest test run = 2.71E-04 -8.21E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 4.17E-04 5.03E-04

Biomass - Stoker

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.52E-05 -1.11E+01

Std Deviation of top performer = 5.87E-06 3.59E-01

Skewness = 1.72 1.71

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

2 2

Highest test run = 2.20E-05 -1.07E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 4.86E-05 1.12E-04

Coal - FB

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 9.05E-06 -1.16E+01

Std Deviation of top performer = 2.87E-06 3.32E-01

Skewness = -0.13 -0.60

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.19E-05 -1.13E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.54E-05 5.76E-05

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-5 : UPL Calculations for New Sources

Parameters

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Total Mass 

PCDD/PCDF

(ng/dscm @ 7% O2)

Coal - PC

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.04E-03 -6.87E+00

Std Deviation of top performer = 7.60E-05 7.23E-02

Skewness = 1.18 1.12

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.12E-03 -6.79E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.47E-03 1.56E-03

Coal - Stoker

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.52E-03 -6.50E+00

Std Deviation of top performer = 2.30E-04 1.46E-01

Skewness = 1.56 1.51

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.78E-03 -6.33E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 2.82E-03 3.46E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-6 : UPL Calculations for New Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Liquid

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.77E-03 -6.35E+00

Std Deviation of top performer = 3.86E-04 2.34E-01

Skewness = -1.55 -1.60

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.05E-03 -6.19E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 3.96E-03 6.59E-03

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.21E-01 -2.19E+00

Std Deviation of top performer = 5.12E-02 5.12E-01

Skewness = -1.73 -1.73

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.51E-01 -1.89E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 4.12E-01 2.06E+00

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-6 : UPL Calculations for New Sources

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.27E-02 -4.37E+00

Std Deviation of top performer = 2.12E-18 0.00E+00

Skewness = -2.45 #DIV/0!

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal #DIV/0!

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.27E-02 -4.37E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.27E-02 1.27E-02

Gas 2

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 4.50E-02 -3.18E+00

Std Deviation of top performer = 2.03E-02 5.02E-01

Skewness = -0.30 -0.92

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 6.46E-02 -2.74E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.60E-01 7.23E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-6 : UPL Calculations for New Sources

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Dutch Oven

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.63E-01 -1.88E+00

Std Deviation of top performer = 6.36E-02 4.40E-01

Skewness = -0.88 -1.26

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.19E-01 -1.52E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 5.24E-01 1.87E+00

Biomass - Fluidized Bed

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 3.00E-02 -3.55E+00

Std Deviation of top performer = 1.09E-02 3.38E-01

Skewness = 1.69 1.66

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 4.25E-02 -3.16E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 9.17E-02 1.97E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-6 : UPL Calculations for New Sources

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Fuel Cell

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.79E-02 -5.06E+00

Std Deviation of top performer = 1.65E-02 2.44E+00

Skewness = -0.61 -1.65

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 3.31E-02 -3.41E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.12E-01 6.78E+03

Biomass - Stoker 35

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.93E-02 -3.61E+00

Std Deviation of top performer = 1.46E-02 4.63E-01

Skewness = 1.67 1.59

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 4.61E-02 -3.08E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 1.12E-01 3.77E-01

Coal - FB

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.91E-03 -6.26E+00

Std Deviation of top performer = 2.34E-04 1.19E-01

Skewness = 1.51 1.46

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.18E-03 -6.13E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 3.25E-03 3.75E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix F-6 : UPL Calculations for New Sources

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Coal - PC

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 1.82E-02 -4.04E+00

Std Deviation of top performer = 6.13E-03 3.16E-01

Skewness = 1.66 1.61

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.52E-02 -3.68E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 5.30E-02 1.06E-01

Coal - Stoker

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top performer = 2.53E-03 -6.00E+00

Std Deviation of top performer = 5.86E-04 2.22E-01

Skewness = 1.51 1.41

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.20E-03 -5.74E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top performer (test runs) = 5.87E-03 8.79E-03

Yellow highlight indicates the distribution (either normal or lognormal)
MACT Floor by Fuel Type

Parameters

PM 

Filterable

(lb/mmBtu) Hg HCl CO

D/F 

total mass

D/F 

TEQ

Total Count of 

Units in 

Subcategory

Biomass 239

No. of sources = 108 42 51

No. in MACT floor = 13 6 7

Coal 525

No. of sources = 335 265 296

No. in MACT floor = 41 32 36

Liquid 791

No. of sources = 81 173 185 106 14 14

No. in MACT floor = 10 21 23 13 2 2

Gas 1 10775

No. of sources = 143 13 10 753 7 7

No. in MACT floor = 18 2 2 91 1 1

Gas 1 - metallurgical furnaces 749

No. of sources = 9 7 9 14 7 7

No. in MACT floor = 2 1 2 2 1 1

Gas 2 196

No. of sources = 13 8 8 74 5 5

No. in MACT floor = 2 1 1 9 1 1

Parameters

CO

(ppm @ 3% 

O2)

Dioxin/Fura

ns (Total 

Mass)

ppm@ 3% 

O2)

Dioxin/Fura

ns (TEQ)

ppm@ 3% 

O2)

Total Count of 

Units in 

Subcategory

Biomass - Dutch Oven 40

No. of sources = 13 2 2

No. in MACT floor = 2 1 1

Biomass - Fluidized Bed 7

No. of sources = 1 1 1

No. in MACT floor = 1 1 1

Biomass - Fuel Cell 16

No. of sources = 11 5 5

No. in MACT floor = 5 5 5

Biomass - Stoker 176

No. of sources = 71 3 3

No. in MACT floor = 9 1 1

Coal - FB 26

No. of sources = 12 8 8

No. in MACT floor = 5 5 5

Coal - PC 180

No. of sources = 39 8 8

No. in MACT floor = 5 1 1

Coal - Stoker 319

No. of sources = 45 8 8

No. in MACT floor = 6 1 1

Appendix G-1: Summary of Number of Sources with Test Data and Top 12 Percent 

under Alternative Solid Waste Definition
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

FLUSSugarCorp Boiler No. 7

Mercury 

(Hg) Biomass 9.73E-08 1 YES

FLSmurfit-Stone 5PB

Mercury 

(Hg) Biomass 2.05E-07 2 YES

NYIntlPaperTiconde

roga PB1

Mercury 

(Hg) Biomass 2.27E-07 3 YES

NDCargillWestFarg

o

Foster Wheeler 

Boiler (EU43)

Mercury 

(Hg) Biomass 2.30E-07 4 YES

NCGPRoxboro

ES-1 Wood fired 

Boiler

Mercury 

(Hg) Biomass 2.67E-07 5 YES

FLSugarCaneGrow

ersCoop Boiler No. 8

Mercury 

(Hg) Biomass 3.40E-07 6 YES

TXMeadWestvacoE

vadale 21-2105

Mercury 

(Hg) Biomass 3.73E-07 7 NO

HIPuuneneSugarMil

l Boiler 1

Mercury 

(Hg) Biomass 4.26E-07 8 NO

HIPuuneneSugarMil

l Boiler 2

Mercury 

(Hg) Biomass 4.26E-07 9 NO

SCNewSouthCamd

en WWB1

Mercury 

(Hg) Biomass 4.39E-07 10 NO

MNDESPHansONy

man EU007

Mercury 

(Hg) Biomass 4.43E-07 11 NO

SCNewSouthCoCo

nway WWB1

Mercury 

(Hg) Biomass 4.76E-07 12 NO

ORRoseburgForest

Dillard Boiler #6

Mercury 

(Hg) Biomass 5.04E-07 13 NO

ARPotlatchForestW

arren Wellons Boiler

Mercury 

(Hg) Biomass 5.41E-07 14 NO

GAInternationalPap

erAugustaMills PB3A

Mercury 

(Hg) Biomass 5.57E-07 15 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ALIPCourtland

No. 1 Combination 

Boiler / 11CU101

Mercury 

(Hg) Biomass 6.08E-07 16 NO

ARWeyerhaeuserDi

erksMill SN-45

Mercury 

(Hg) Biomass 6.24E-07 17 NO

SCSmurfitStone Unit 15: Boiler #3

Mercury 

(Hg) Biomass 6.67E-07 18 NO

ORRoseburgRiddle

2 Boiler #2

Mercury 

(Hg) Biomass 7.45E-07 19 NO

GAGPCelluloseBru

nswick

U700 -- No. 4 

Power Boiler

Mercury 

(Hg) Biomass 7.66E-07 20 NO

ARAnthonyForestPr

oducts SN-12

Mercury 

(Hg) Biomass 8.24E-07 21 NO

NCLPRoaringRiver Boiler #2

Mercury 

(Hg) Biomass 9.13E-07 22 NO

MSWeyerhaeuserBr

uce

AA-002 No. 2 

Boiler

Mercury 

(Hg) Biomass 9.93E-07 23 NO

IDMoyieSprings 

Lumber420 HFB1

Mercury 

(Hg) Biomass 1.02E-06 24 NO

MSGPNewAugusta

AA-015 Power 

Boiler

Mercury 

(Hg) Biomass 1.10E-06 25 NO

GARayonierJesupM

ill PB01

Mercury 

(Hg) Biomass 1.19E-06 26 NO

ARGBPMorrilton SN-04

Mercury 

(Hg) Biomass 1.22E-06 27 NO

GAGPWarmSprings

EU600 Wood Fuel 

Boiler

Mercury 

(Hg) Biomass 1.36E-06 28 NO

ORRoseburgCoquill

e Boiler 1

Mercury 

(Hg) Biomass 1.41E-06 29 NO

ORRoseburgForest

Dillard Boiler #2

Mercury 

(Hg) Biomass 1.64E-06 30 NO

ORRosboroSpringfi

eld DV 01.1

Mercury 

(Hg) Biomass 1.65E-06 31 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

FLUSSugarCorp Boiler No. 4

Mercury 

(Hg) Biomass 1.77E-06 32 NO

WAWeyerhaeuser_

Raymond

Hog Fuel Boiler 

EU1

Mercury 

(Hg) Biomass 1.86E-06 33 NO

ORRoseburgForest

Dillard Boiler #1

Mercury 

(Hg) Biomass 2.28E-06 34 NO

WAGraysHarborPa

per No. 8 Boiler (EU1)

Mercury 

(Hg) Biomass 2.42E-06 35 NO

WASimpsonLumber

Company EU1

Mercury 

(Hg) Biomass 2.50E-06 36 NO

WAGraysHarborPa

per No. 6 Boiler (EU2)

Mercury 

(Hg) Biomass 2.74E-06 37 NO

ORWeyerhaeuserC

oWarrentonLumber

Mill 3-HFB

Mercury 

(Hg) Biomass 2.92E-06 38 NO

MIWhitePineElectric IBW Boiler

Mercury 

(Hg) Biomass 2.97E-06 39 NO

FLOsceolaFarms Boiler No. 4

Mercury 

(Hg) Biomass 3.21E-06 40 NO

FLOsceolaFarms Boiler No. 2

Mercury 

(Hg) Biomass 6.30E-06 41 NO

NCLPRoaringRiver Boiler #3

Mercury 

(Hg) Biomass 8.00E-06 42 NO

IAUofIowa EP7 Boiler 11

Mercury 

(Hg) Coal 1.43E-08 1 YES

MITBSimonPowerPl

ant Unit 4

Mercury 

(Hg) Coal 2.87E-08 2 YES

IAArchersDanielsMi

dlandDesMoines Asea Boiler #1

Mercury 

(Hg) Coal 3.84E-08 3 YES

IARoquetteAmerica

Circulating Fluidized 

Bed Boiler (121)

Mercury 

(Hg) Coal 6.17E-08 4 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

INPurdueUniverisity Boiler 5

Mercury 

(Hg) Coal 1.23E-07 5 YES

ILPolyOne B1

Mercury 

(Hg) Coal 1.23E-07 6 YES

MITBSimonPowerPl

ant Unit 2

Mercury 

(Hg) Coal 1.44E-07 7 YES

MNADMCornDivisio

n

Coal Boiler #1 

EU049

Mercury 

(Hg) Coal 1.59E-07 8 YES

MNADMCornDivisio

n

Coal Boiler #2 

EU050

Mercury 

(Hg) Coal 1.59E-07 9 YES

MITBSimonPowerPl

ant Unit 1

Mercury 

(Hg) Coal 1.84E-07 10 YES

NCTysonHarmony TYS-ES-21

Mercury 

(Hg) Coal 2.43E-07 11 YES

IDAmalgamatedSug

arCoTwinFalls S-B1

Mercury 

(Hg) Coal 2.56E-07 12 YES

AKDoyonUtilities_A

K 4

Mercury 

(Hg) Coal 3.52E-07 13 YES

IAADMCornProcess

ingCR EU-501B

Mercury 

(Hg) Coal 3.58E-07 14 YES

VAUniversityofVirgi

nia 7103-1-01R

Mercury 

(Hg) Coal 3.70E-07 15 YES

VADukeEnergyNarr

ows Boiler #1

Mercury 

(Hg) Coal 3.83E-07 16 YES

MINeenahPaperMI Boiler 1

Mercury 

(Hg) Coal 3.94E-07 17 YES

OHAppletonIdeas Boiler 4 (B003)

Mercury 

(Hg) Coal 3.94E-07 18 YES

TNNissanSmyrna Boiler 3

Mercury 

(Hg) Coal 4.17E-07 19 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCUNCCogen ES-001

Mercury 

(Hg) Coal 4.18E-07 20 YES

INTateLyleSagamor

e 31B1

Mercury 

(Hg) Coal 4.31E-07 21 YES

OKGPMuskogeeMill B-3

Mercury 

(Hg) Coal 4.67E-07 22 YES

TNCargillMemphis Stoker Boiler 8001

Mercury 

(Hg) Coal 4.67E-07 23 YES

WIWausauRhine B26

Mercury 

(Hg) Coal 4.80E-07 24 YES

ALIPCourtland

No.2 Combination 

Boiler / 11CU201

Mercury 

(Hg) Coal 5.38E-07 25 YES

VADukeEnergyNarr

ows Boiler #2

Mercury 

(Hg) Coal 5.39E-07 26 YES

TNNissanSmyrna Boiler 2

Mercury 

(Hg) Coal 5.47E-07 27 YES

PANorfolkSouthern 031

Mercury 

(Hg) Coal 6.60E-07 28 YES

PANorfolkSouthern 032

Mercury 

(Hg) Coal 6.60E-07 29 YES

PANorfolkSouthern 033

Mercury 

(Hg) Coal 6.60E-07 30 YES

MNRochesterUtilitie

s EU003

Mercury 

(Hg) Coal 6.61E-07 31 YES

VADukeEnergyNarr

ows Boiler #7

Mercury 

(Hg) Coal 6.71E-07 32 YES

ILBungeDanville CFB Boiler

Mercury 

(Hg) Coal 7.04E-07 33 NO

AKDoyonUtilities_A

K 7

Mercury 

(Hg) Coal 7.22E-07 34 NO

IAUofNorthernIowa Boiler #3

Mercury 

(Hg) Coal 7.68E-07 35 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VARadfordArmyAm

munitionPlant Boiler No. 5

Mercury 

(Hg) Coal 7.74E-07 36 NO

OHCargillSidney B002

Mercury 

(Hg) Coal 7.93E-07 37 NO

GAInternationalPap

erAugustaMills PB1A

Mercury 

(Hg) Coal 8.41E-07 38 NO

TNEastman_NO_C

BIDATA Boiler 30

Mercury 

(Hg) Coal 8.89E-07 39 NO

NJVinelandMuniEle

ctric-HowardDown Unit 10

Mercury 

(Hg) Coal 8.97E-07 40 NO

VASmurfitStoneWe

stpt PB08

Mercury 

(Hg) Coal 9.48E-07 41 NO

NCMCASCherryPoi

nt CP-152-BOIL-02

Mercury 

(Hg) Coal 9.50E-07 42 NO

VAVirginiaPolytechn

ic Boiler 11

Mercury 

(Hg) Coal 1.00E-06 43 NO

WVPPGMartinsville R011-Boiler 3

Mercury 

(Hg) Coal 1.02E-06 44 NO

WIGreenBayPacka

gingMillDivision

Boiler B26- Coal 

Fired Boiler

Mercury 

(Hg) Coal 1.03E-06 45 NO

IDTASCONampa

Babcock and 

Wilcox (B&W) #1

Mercury 

(Hg) Coal 1.04E-06 46 NO

IDTASCONampa

Babcock and 

Wilcox (B&W) #2

Mercury 

(Hg) Coal 1.04E-06 47 NO

MNRochesterUtilitie

s EU002

Mercury 

(Hg) Coal 1.06E-06 48 NO

IDAmalgamatedSug

arCoTwinFalls S-B2

Mercury 

(Hg) Coal 1.13E-06 49 NO

NDMinnDakFarmer

s

Babcock and 

Wilcox Boiler #5

Mercury 

(Hg) Coal 1.14E-06 50 NO

IDTASCOPaul Erie City Boiler

Mercury 

(Hg) Coal 1.19E-06 51 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VADukeEnergyNarr

ows Boiler #4

Mercury 

(Hg) Coal 1.20E-06 52 NO

MOAnheuserBusch Boiler 5

Mercury 

(Hg) Coal 1.21E-06 53 NO

MOAnheuserBusch Boiler 1

Mercury 

(Hg) Coal 1.25E-06 54 NO

GAGPSRMRiincon EU BO01

Mercury 

(Hg) Coal 1.26E-06 55 NO

VAMeadWestVacoCovingtonVA PWR006Mercury 

(Hg) Coal 1.29E-06 56 NO

VAMeadWestVacoCovingtonVA PWR007Mercury 

(Hg) Coal 1.29E-06 57 NO

VAMeadWestVacoCovingtonVA PWR008Mercury 

(Hg) Coal 1.29E-06 58 NO

VAMeadWestVacoCovingtonVA PWR009Mercury 

(Hg) Coal 1.29E-06 59 NO

WIAppleton

B22 Coal Fired 

Boiler

Mercury 

(Hg) Coal 1.30E-06 60 NO

INSABICInnovative

Plastics 01-001 BW1 Boiler

Mercury 

(Hg) Coal 1.34E-06 61 NO

INSABICInnovative

Plastics 01-001 BW2 Boiler

Mercury 

(Hg) Coal 1.34E-06 62 NO

OHSmartPapersHol

dingsLLC B020

Mercury 

(Hg) Coal 1.39E-06 63 NO

WIGPGreenBay281

8

B25 - Stoker Boiler 

#5

Mercury 

(Hg) Coal 1.39E-06 64 NO

WIGPGreenBay281

8

B26 - Stoker Boiler 

#6

Mercury 

(Hg) Coal 1.39E-06 65 NO

WIGPGreenBay281

8

B27 - Cyclone 

Boiler #7

Mercury 

(Hg) Coal 1.39E-06 66 NO

WIGPGreenBay281

8

B28 - Stoker Boiler 

#8

Mercury 

(Hg) Coal 1.39E-06 67 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VADukeEnergyNarr

ows Boiler #5

Mercury 

(Hg) Coal 1.41E-06 68 NO

ALGeorgiaPacificNa

heola Z016 - CB2

Mercury 

(Hg) Coal 1.43E-06 69 NO

MNRochesterUtilitie

s EU001

Mercury 

(Hg) Coal 1.47E-06 70 NO

VADukeEnergyNarr

ows Boiler #3

Mercury 

(Hg) Coal 1.47E-06 71 NO

MIHollandBPW Unit 3

Mercury 

(Hg) Coal 1.49E-06 72 NO

GACaraustar CB01

Mercury 

(Hg) Coal 1.54E-06 73 NO

WVPPGMartinsville R072-Boiler 5

Mercury 

(Hg) Coal 1.55E-06 74 NO

WIWausauRhine B20

Mercury 

(Hg) Coal 1.60E-06 75 NO

WIWausauRhine B21

Mercury 

(Hg) Coal 1.60E-06 76 NO

WIWausauRhine B22

Mercury 

(Hg) Coal 1.60E-06 77 NO

WIWausauRhine B23

Mercury 

(Hg) Coal 1.60E-06 78 NO

OHDukeEnergyGen

erationCincinnati

B022 (Boiler #4, IG4A)Mercury 

(Hg) Coal 1.71E-06 79 NO

MNAmericanCrystal

Crookston Boiler 1

Mercury 

(Hg) Coal 1.72E-06 80 NO

MNWausauPaperBrainerd EU 002Mercury 

(Hg) Coal 1.72E-06 81 NO

MNWausauPaperBrainerd EU 003Mercury 

(Hg) Coal 1.72E-06 82 NO

IDTASCOPaul

Babcock and 

Wilcox (B&W) 

Boiler

Mercury 

(Hg) Coal 1.76E-06 83 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WIDairylandPowerAlma Alma 1Mercury 

(Hg) Coal 1.78E-06 84 NO

WIDairylandPowerAlma Alma 2Mercury 

(Hg) Coal 1.78E-06 85 NO

WIDairylandPowerAlma Alma 3Mercury 

(Hg) Coal 1.78E-06 86 NO

MAUMass EU#3

Mercury 

(Hg) Coal 1.79E-06 87 NO

MAUMass EU#4

Mercury 

(Hg) Coal 1.79E-06 88 NO

MAUMass EU#5

Mercury 

(Hg) Coal 1.79E-06 89 NO

OHCargillSidney B001

Mercury 

(Hg) Coal 1.80E-06 90 NO

MIPharma&Upjohn1

180 Boiler 3

Mercury 

(Hg) Coal 1.82E-06 91 NO

OHPainesvilleMunic

ipalElectric B004

Mercury 

(Hg) Coal 1.84E-06 92 NO

WIThilmanyLLC B11

Mercury 

(Hg) Coal 1.85E-06 93 NO

WIThilmanyLLC B09

Mercury 

(Hg) Coal 1.85E-06 94 NO

WINewPageWisconsinRapidsPower Boiler 2 - 

B20

Mercury 

(Hg) Coal 1.85E-06 95 NO

GACargillGainesville B001Mercury 

(Hg) Coal 1.90E-06 96 NO

OHMortonSaltRittm

an

B003 - Coal-Fired 

Boiler #1

Mercury 

(Hg) Coal 1.90E-06 97 NO

VARadfordArmyAm

munitionPlant Boiler No. 3

Mercury 

(Hg) Coal 1.90E-06 98 NO

NCUNCCogen ES-002

Mercury 

(Hg) Coal 1.93E-06 99 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IAMuscatinePowera

ndWater Unit 7

Mercury 

(Hg) Coal 1.96E-06 100 NO

OKGPMuskogeeMill B-4

Mercury 

(Hg) Coal 2.00E-06 101 NO

MOIPLBlueValley Unit 1

Mercury 

(Hg) Coal 2.09E-06 102 NO

PABayValleyFoods

Pittsburgh Boiler No. 3

Mercury 

(Hg) Coal 2.09E-06 103 NO

PABayValleyFoods

Pittsburgh Boiler No. 4

Mercury 

(Hg) Coal 2.09E-06 104 NO

MDDeptofNavySup

portFacilityIndianHe

ad

PTO - 873 - E3 (3-

0006) (Boiler 3)

Mercury 

(Hg) Coal 2.10E-06 105 NO

OHMortonSaltRittm

an

B002 - Coal-Fired 

Boiler #2

Mercury 

(Hg) Coal 2.10E-06 106 NO

NCBlueRidgePaper G11040

Mercury 

(Hg) Coal 2.10E-06 107 NO

MOAnheuserBusch Boiler 8

Mercury 

(Hg) Coal 2.13E-06 108 NO

MITBSimonPowerPl

ant Unit 3

Mercury 

(Hg) Coal 2.13E-06 109 NO

TNEastman_NO_C

BIDATA Boiler 31

Mercury 

(Hg) Coal 2.13E-06 110 NO

ALGeorgiaPacificNa

heola Z015 - CB1

Mercury 

(Hg) Coal 2.14E-06 111 NO

WYGeneralChemic

al GR-2-L (C BOILER)

Mercury 

(Hg) Coal 2.18E-06 112 NO

VARadfordArmyAm

munitionPlant Boiler No. 2

Mercury 

(Hg) Coal 2.26E-06 113 NO

ILPrairiePowerPearl B1

Mercury 

(Hg) Coal 2.27E-06 114 NO

WINewPageWisconsinRapidsPower Boiler 1 - 

B21

Mercury 

(Hg) Coal 2.28E-06 115 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHUofCincinnati B108

Mercury 

(Hg) Coal 2.28E-06 116 NO

NYAESWestover Boiler 13

Mercury 

(Hg) Coal 2.29E-06 117 NO

VAGPBigIsland270

3

PWR04 - No. 4 

Power Boiler

Mercury 

(Hg) Coal 2.29E-06 118 NO

VAPhilipMorrisPark

500 B3

Mercury 

(Hg) Coal 2.34E-06 119 NO

MOIP&LMissouriCit

y Unit 1

Mercury 

(Hg) Coal 2.35E-06 120 NO

MOIP&LMissouriCit

y Unit 2

Mercury 

(Hg) Coal 2.35E-06 121 NO

MOBASFHannibal Coal Fired Boiler #5

Mercury 

(Hg) Coal 2.38E-06 122 NO

VAINVISTAWaynes

boro

2-205 (B#2) Boiler 

#2

Mercury 

(Hg) Coal 2.46E-06 123 NO

WVUCCSouthCharl

eston B25

Mercury 

(Hg) Coal 2.46E-06 124 NO

MOMallinckrodt Boiler 6

Mercury 

(Hg) Coal 2.47E-06 125 NO

WINewPageBiron B24

Mercury 

(Hg) Coal 2.54E-06 126 NO

TNOakRidge-Y12 Boiler/Unit 31

Mercury 

(Hg) Coal 2.57E-06 127 NO

OHShelbyMuniLight

Plant B008

Mercury 

(Hg) Coal 2.63E-06 128 NO

SCClemson 04-B04

Mercury 

(Hg) Coal 2.63E-06 129 NO

OKGPMuskogeeMill B-2

Mercury 

(Hg) Coal 2.67E-06 130 NO

TNBowaterNewspri

nt Power Boiler No. 3

Mercury 

(Hg) Coal 2.77E-06 131 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WIWausau

# 6 Power Boiler 

(B20)

Mercury 

(Hg) Coal 2.79E-06 132 NO

OHShelbyMuniLight

Plant B007

Mercury 

(Hg) Coal 2.80E-06 133 NO

VADukeEnergyNarr

ows Boiler #6

Mercury 

(Hg) Coal 2.83E-06 134 NO

WIThilmanyPapers

NicoletMill B23

Mercury 

(Hg) Coal 2.86E-06 135 NO

WIThilmanyPapers

NicoletMill B24

Mercury 

(Hg) Coal 2.86E-06 136 NO

NYCornellUniversity B1

Mercury 

(Hg) Coal 2.95E-06 137 NO

TNEastman_NO_C

BIDATA Boiler 25

Mercury 

(Hg) Coal 2.97E-06 138 NO

WIWausau

# 5 Power Boiler 

(B24)

Mercury 

(Hg) Coal 3.08E-06 139 NO

NCBlueRidgePaper G11039

Mercury 

(Hg) Coal 3.13E-06 140 NO

PAPHGlatfelter PB4

Mercury 

(Hg) Coal 3.14E-06 141 NO

PAPHGlatfelter PB1

Mercury 

(Hg) Coal 3.15E-06 142 NO

PAPHGlatfelter PB3

Mercury 

(Hg) Coal 3.15E-06 143 NO

ILRockIslandArsena

l Boiler #4

Mercury 

(Hg) Coal 3.15E-06 144 NO

TNEastman_NO_C

BIDATA Boiler 27

Mercury 

(Hg) Coal 3.23E-06 145 NO

ILADMPeoria EU-PH101

Mercury 

(Hg) Coal 3.25E-06 146 NO

ILADMPeoria EU-PH102

Mercury 

(Hg) Coal 3.25E-06 147 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WYGeneralChemic

al

GR-3-W (D 

BOILER)

Mercury 

(Hg) Coal 3.27E-06 148 NO

WVSunocoIncNeal

PlantKenova B602, Coal Boiler

Mercury 

(Hg) Coal 3.30E-06 149 NO

MOIPLBlueValley Unit 2

Mercury 

(Hg) Coal 3.32E-06 150 NO

GAInternationalPap

erAugustaMills PB2A

Mercury 

(Hg) Coal 3.35E-06 151 NO

ILRockIslandArsena

l

NBN 12602 (Boiler 

#1)

Mercury 

(Hg) Coal 3.36E-06 152 NO

MIManistiquePaper EUBLR001

Mercury 

(Hg) Coal 3.37E-06 153 NO

MIManistiquePaper EUBLR002

Mercury 

(Hg) Coal 3.37E-06 154 NO

ILADMQuincy EU-5003

Mercury 

(Hg) Coal 3.42E-06 155 NO

ILADMQuincy EU-5004

Mercury 

(Hg) Coal 3.42E-06 156 NO

MIHollandBPW Unit 4

Mercury 

(Hg) Coal 3.45E-06 157 NO

VAVirginiaPolytechn

ic Boiler 7

Mercury 

(Hg) Coal 3.50E-06 158 NO

MNHibbing Unit 2A

Mercury 

(Hg) Coal 3.50E-06 159 NO

PABayValleyFoods

Pittsburgh Boiler No. 1

Mercury 

(Hg) Coal 3.55E-06 160 NO

PABayValleyFoods

Pittsburgh Boiler No. 2

Mercury 

(Hg) Coal 3.55E-06 161 NO

VAPhilipMorrisPark

500 B2

Mercury 

(Hg) Coal 3.57E-06 162 NO

MNWausauPaperBrainerd EU 004Mercury 

(Hg) Coal 3.67E-06 163 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNHibbing Unit 1A

Mercury 

(Hg) Coal 3.70E-06 164 NO

PADomtarJohnsonb

urg #81 Coal Boiler

Mercury 

(Hg) Coal 3.77E-06 165 NO

PADomtarJohnsonb

urg #82 Coal Boiler

Mercury 

(Hg) Coal 3.77E-06 166 NO

MNAmericanCrystal

Moorhead Boiler 3

Mercury 

(Hg) Coal 3.78E-06 167 NO

TNViskase Boiler 1

Mercury 

(Hg) Coal 3.80E-06 168 NO

TNViskase Boiler 2

Mercury 

(Hg) Coal 3.80E-06 169 NO

NCMillerCoors

ES-1 Coal/No. 2 & 6 

Fuel Oil Boiler

Mercury 

(Hg) Coal 3.86E-06 170 NO

OHUSEnrichmentC

orpPiketon X-600 Boiler No. 3

Mercury 

(Hg) Coal 3.92E-06 171 NO

WIDomtarNekoosa B20 - Boiler No. 1

Mercury 

(Hg) Coal 3.93E-06 172 NO

WIDomtarNekoosa B21 - Boiler No. 2

Mercury 

(Hg) Coal 3.93E-06 173 NO

WIDomtarNekoosa B22 - Boiler No. 7

Mercury 

(Hg) Coal 3.93E-06 174 NO

WIDomtarNekoosa B24 - Boiler No. 10

Mercury 

(Hg) Coal 3.93E-06 175 NO

ILAbbottAbbottPark Unit 5AP

Mercury 

(Hg) Coal 3.94E-06 176 NO

MICityofEscanaba EUBOILER#1

Mercury 

(Hg) Coal 4.00E-06 177 NO

NCKapStone PB1

Mercury 

(Hg) Coal 4.01E-06 178 NO

MNDESPHansONy

man EU003

Mercury 

(Hg) Coal 4.09E-06 179 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MDDeptofNavySup

portFacilityIndianHe

ad

PTO - 873 - E2 (3-

0005) (Boiler 2)

Mercury 

(Hg) Coal 4.10E-06 180 NO

MIPharma&Upjohn1

178

EUEBLR43-5 

(Boiler No. 5)

Mercury 

(Hg) Coal 4.11E-06 181 NO

NCBlueRidgePaper G11037

Mercury 

(Hg) Coal 4.24E-06 182 NO

NCBlueRidgePaper G11038

Mercury 

(Hg) Coal 4.24E-06 183 NO

MNDESPHansONy

man EU002

Mercury 

(Hg) Coal 4.27E-06 184 NO

VAPhilipMorrisMC PC

Mercury 

(Hg) Coal 4.37E-06 185 NO

OHAkronThermalEn

ergy Boiler #32 (B001)

Mercury 

(Hg) Coal 4.37E-06 186 NO

OHAppletonIdeas Boiler 2 (B002)

Mercury 

(Hg) Coal 4.38E-06 187 NO

OHCampbellsSoup

Co B001

Mercury 

(Hg) Coal 4.60E-06 188 NO

OHCampbellsSoup

Co B002

Mercury 

(Hg) Coal 4.60E-06 189 NO

WVATKRocketCent

er

NB2766 W-17479-

W (Boiler 17)

Mercury 

(Hg) Coal 4.76E-06 190 NO

MIPharma&Upjohn1

178

EUEBLR43-2 

(Boiler No. 2)

Mercury 

(Hg) Coal 4.79E-06 191 NO

VARadfordArmyAm

munitionPlant Boiler No. 4

Mercury 

(Hg) Coal 4.80E-06 192 NO

NCMCASCherryPoi

nt CP-152-BOIL-01

Mercury 

(Hg) Coal 4.83E-06 193 NO

NYCornellUniversity B8

Mercury 

(Hg) Coal 4.83E-06 194 NO

KYISPChemicals 0AA (Riley)

Mercury 

(Hg) Coal 4.91E-06 195 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WVBayerInstitute Boiler #10

Mercury 

(Hg) Coal 4.93E-06 196 NO

WVBayerInstitute Boiler #11

Mercury 

(Hg) Coal 4.93E-06 197 NO

WVBayerInstitute Boiler #12

Mercury 

(Hg) Coal 4.93E-06 198 NO

OHShelbyMuniLight

Plant B006

Mercury 

(Hg) Coal 4.98E-06 199 NO

MDNewPage-Luke No. 25

Mercury 

(Hg) Coal 5.21E-06 200 NO

NCMillerCoors

ES-2 Coal/No. 2 & 6 

Fuel Oil Boiler

Mercury 

(Hg) Coal 5.25E-06 201 NO

TNDuPontOldHickor

yPlant #24 Boiler

Mercury 

(Hg) Coal 5.27E-06 202 NO

PAARGBradford 37

Mercury 

(Hg) Coal 5.51E-06 203 NO

NCCampLejeuneM

CB A-HP-1700-01

Mercury 

(Hg) Coal 5.65E-06 204 NO

NCCampLejeuneM

CB A-HP-1700-02

Mercury 

(Hg) Coal 5.65E-06 205 NO

TNDuPontOldHickor

yPlant #20 Boiler

Mercury 

(Hg) Coal 5.67E-06 206 NO

MOTrigenKansasCit

y Boiler 6

Mercury 

(Hg) Coal 5.72E-06 207 NO

MOTrigenKansasCit

y Boiler 8

Mercury 

(Hg) Coal 5.76E-06 208 NO

FLIPPensacola

Power Boiler 3 / EU 

ID 33

Mercury 

(Hg) Coal 5.85E-06 209 NO

OHBataviaTransmis

sions Boiler 2 (B002)

Mercury 

(Hg) Coal 6.00E-06 210 NO

OHPainesvilleMunic

ipalElectric B001

Mercury 

(Hg) Coal 6.04E-06 211 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHSmartPapersHol

dingsLLC B010

Mercury 

(Hg) Coal 6.16E-06 212 NO

INSABICInnovative

Plastics 09-002 Erie Boiler

Mercury 

(Hg) Coal 6.24E-06 213 NO

INSABICInnovative

Plastics

09-002 Lasker 

Boiler

Mercury 

(Hg) Coal 6.24E-06 214 NO

FLIPPensacola

Power Boiler 4 / EU 

ID 37

Mercury 

(Hg) Coal 6.30E-06 215 NO

OHPainesvilleMunic

ipalElectric B003

Mercury 

(Hg) Coal 6.34E-06 216 NO

MIMenominee #3 Boiler

Mercury 

(Hg) Coal 6.60E-06 217 NO

ALCargill-Decatur Keeler (S-407)

Mercury 

(Hg) Coal 6.63E-06 218 NO

OHMedicalCenterC

o1915 B003

Mercury 

(Hg) Coal 6.83E-06 219 NO

OHMedicalCenterC

o1915 B004

Mercury 

(Hg) Coal 6.83E-06 220 NO

TNBowaterNewspri

nt Power Boiler No. 1

Mercury 

(Hg) Coal 6.93E-06 221 NO

NCCampLejeuneM

CB A-HP-1700-03

Mercury 

(Hg) Coal 6.95E-06 222 NO

NCCampLejeuneM

CB A-HP-1700-04

Mercury 

(Hg) Coal 6.95E-06 223 NO

WVDuPontWashing

tonWorks P05

Mercury 

(Hg) Coal 7.14E-06 224 NO

ILDukeEnergyTusco

la Unit 1

Mercury 

(Hg) Coal 7.19E-06 225 NO

OHUSEnrichmentC

orpPiketon X-600 Boiler No. 1

Mercury 

(Hg) Coal 7.39E-06 226 NO

VAGPJarrattFiberbo

ard

EP-15 No. 3 Keeler 

Boiler

Mercury 

(Hg) Coal 7.40E-06 227 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MIEBEddyPaper EUBOILER5

Mercury 

(Hg) Coal 7.43E-06 228 NO

WINewPageBiron B23

Mercury 

(Hg) Coal 7.69E-06 229 NO

OHUSEnrichmentC

orpPiketon X-600 Boiler No. 2

Mercury 

(Hg) Coal 8.06E-06 230 NO

MNHibbing Unit 3A

Mercury 

(Hg) Coal 8.43E-06 231 NO

IAJohnDeereDubuq

ue Boiler 1

Mercury 

(Hg) Coal 8.49E-06 232 NO

IAJohnDeereDubuq

ue Boiler 4

Mercury 

(Hg) Coal 8.49E-06 233 NO

MOColumbiaPower

Plant Boiler Unit 6

Mercury 

(Hg) Coal 8.52E-06 234 NO

MOColumbiaPower

Plant Boiler Unit 7

Mercury 

(Hg) Coal 8.52E-06 235 NO

INNotreDame B-4

Mercury 

(Hg) Coal 8.53E-06 236 NO

WINewPageWhiting B24Mercury 

(Hg) Coal 8.69E-06 237 NO

WVPPGMartinsville R015-Boiler 4

Mercury 

(Hg) Coal 8.85E-06 238 NO

IACentralIAPower

EP1 Unit 1 PC 

Boiler

Mercury 

(Hg) Coal 9.03E-06 239 NO

MDDeptofNavySup

portFacilityIndianHe

ad

PTO - 873 - E1 (3-

0004) (Boiler 1)

Mercury 

(Hg) Coal 9.17E-06 240 NO

PAPennState 31

Mercury 

(Hg) Coal 9.34E-06 241 NO

PAPennState 32

Mercury 

(Hg) Coal 9.34E-06 242 NO

PAPennState 34

Mercury 

(Hg) Coal 9.34E-06 243 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

PAPennState 35

Mercury 

(Hg) Coal 9.34E-06 244 NO

MICityofEscanaba EUBOILER#2

Mercury 

(Hg) Coal 9.48E-06 245 NO

PABellefieldPlant Boiler 3

Mercury 

(Hg) Coal 9.75E-06 246 NO

INTateLyleLafayette

South LA-45

Mercury 

(Hg) Coal 9.86E-06 247 NO

IAUofIowa EP6 Boiler 10

Mercury 

(Hg) Coal 1.00E-05 248 NO

INBungeDecatur B&W (1SP1)

Mercury 

(Hg) Coal 1.05E-05 249 NO

INBungeDecatur Keeler (2SP1)

Mercury 

(Hg) Coal 1.05E-05 250 NO

TNInvistaChattanoo

ga EU002 - Boiler #4

Mercury 

(Hg) Coal 1.22E-05 251 NO

WVDuPontWashing

tonWorks P02

Mercury 

(Hg) Coal 1.37E-05 252 NO

INNotreDame B-2

Mercury 

(Hg) Coal 1.43E-05 253 NO

INNotreDame B-3

Mercury 

(Hg) Coal 1.43E-05 254 NO

WVDuPontWashing

tonWorks P03

Mercury 

(Hg) Coal 1.60E-05 255 NO

WVDuPontWashing

tonWorks P06

Mercury 

(Hg) Coal 1.97E-05 256 NO

MDNewPage-Luke No. 24

Mercury 

(Hg) Coal 1.97E-05 257 NO

DEINVISTA

EU 001 - Coal 

Boiler No. 1

Mercury 

(Hg) Coal 2.80E-05 258 NO

MNVersoPaper EU018 Bros

Mercury 

(Hg) Coal 2.81E-05 259 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

DEINVISTA

EU 003 - Coal 

Boiler No. 3

Mercury 

(Hg) Coal 3.50E-05 260 NO

OHCargillAkron B001

Mercury 

(Hg) Coal 8.03E-05 261 NO

MSDuPontDeLisle1

342

AF-101A (BLR1342)Mercury 

(Hg) Coal 5.36E-04 262 NO

MSDuPontDeLisle1

342

AF-101B (BLR1342)Mercury 

(Hg) Coal 5.36E-04 263 NO

WINewPageKimberl

y B21

Mercury 

(Hg) Coal 1.73E-03 264 NO

WINewPageKimberl

y B22

Mercury 

(Hg) Coal 1.73E-03 265 NO

NCCampLejeuneM

CB C-AS-4151-16

Mercury 

(Hg) Gas 1 9.35E-08 1 YES

CAConocoPhilipsLo

sAng D146 B-202 U90

Mercury 

(Hg) Gas 1 1.21E-07 2 YES

CAExxonMobilTorrance 25F-1AMercury 

(Hg) Gas 1 2.30E-07 3 NO

CAExxonMobilTorrance 25F-1BMercury 

(Hg) Gas 1 2.30E-07 4 NO

CAExxonMobilTorrance 25F-2AMercury 

(Hg) Gas 1 2.30E-07 5 NO

CAExxonMobilTorrance 25F-2BMercury 

(Hg) Gas 1 2.30E-07 6 NO

SCEastmanColombi

a

HTM Heater #3 

(Equip ID 1101)

Mercury 

(Hg) Gas 1 3.35E-07 7 NO

SCMichelinSandyS

prings B:02:01

Mercury 

(Hg) Gas 1 3.55E-07 8 NO

KSCoffeyvilleRefine

ry EU-39-FH0027

Mercury 

(Hg) Gas 1 3.63E-07 9 NO

WYSinclairWyomin

g

Pt 74 #2 H2 Plant 

Heater

Mercury 

(Hg) Gas 1 5.40E-07 10 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WYSinclairWyomin

g Pt 41 #9 HPB

Mercury 

(Hg) Gas 1 7.02E-07 11 NO

CAExxonMobilTorrance 24F-1Mercury 

(Hg) Gas 1 1.59E-06 12 NO

MNStPaulParkRef EU 026

Mercury 

(Hg) Gas 1 1.87E-06 13 NO

ILUSSGraniteCity

No. 8 Galvanizing 

Line Furnace

Mercury 

(Hg) Gas 1 3.32E-08 yes 1 YES

INNucorSteel Cold Mill Annealing

Mercury 

(Hg) Gas 1 1.29E-07 yes 2 NO

INArcelorMittalBurn

sHarbor

Hot Dip Coating 

Line Annealing 

Furnace

Mercury 

(Hg) Gas 1 1.51E-07 yes 3 NO

UTWestinghouse 202

Mercury 

(Hg) Gas 1 7.50E-07 yes 4 NO

INOutokumpuStainl

essPlate

Heppenstall 

Annealing Furnace

Mercury 

(Hg) Gas 1 1.17E-06 yes 5 NO

INAlcoaWarrick

Annealing Furnace 

#15

Mercury 

(Hg) Gas 1 2.68E-06 yes 6 NO

INAlcoaWarrick

Pre-Heat Furnace 

#36

Mercury 

(Hg) Gas 1 2.68E-06 yes 7 NO

SCBMWManufactur

ingCo HB03

Mercury 

(Hg) Gas 2 8.25E-08 1 YES

LAShellChemicaGei

smar Furnace F-S801

Mercury 

(Hg) Gas 2 1.07E-07 2 NO

INTateLyleSagamor

e 21B501

Mercury 

(Hg) Gas 2 1.58E-07 3 NO

INRollsRoyceIndian

apolis 70-65

Mercury 

(Hg) Gas 2 2.51E-07 4 NO

WIGPGreenBay281

8

B29 - Fluidized Bed 

Boiler #9

Mercury 

(Hg) Gas 2 3.64E-07 5 NO

GAGPSRMRiincon EU BO02

Mercury 

(Hg) Gas 2 5.67E-07 6 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MDSeverstalSparro

ws 1BLR (No. 1 Boiler)

Mercury 

(Hg) Gas 2 1.30E-06 7 NO

WVMountainStateC

arbonFollansbee S1

Mercury 

(Hg) Gas 2 6.20E-06 8 NO

MNGPDuluth EU33 Boiler #3

Mercury 

(Hg) Liquid 5.87E-08 1 YES

MEFPLEnergyWym

an Unit #5

Mercury 

(Hg) Liquid 8.60E-08 2 YES

PABoeingRidleyPar

k 033

Mercury 

(Hg) Liquid 1.22E-07 3 YES

NYConEd59thStSta

tionNewYork Boiler 118

Mercury 

(Hg) Liquid 1.39E-07 4 YES

NJVinelandMuniEle

ctric-HowardDown Unit 9

Mercury 

(Hg) Liquid 3.87E-07 5 YES

MESDWarrenSome

rset Package Boiler

Mercury 

(Hg) Liquid 3.92E-07 6 YES

CTElectric Boat EMU 18

Mercury 

(Hg) Liquid 4.36E-07 7 YES

CTElectric Boat EMU 17

Mercury 

(Hg) Liquid 4.36E-07 8 YES

INUSSteelGaryWor

ks O4B10459

Mercury 

(Hg) Liquid 7.79E-07 9 YES

TNMilanArmyAmmu

nitionPlant

F52L-1, Source #27-

0010-30

Mercury 

(Hg) Liquid 2.15E-06 10 YES

TNMilanArmyAmmu

nitionPlant

A15L-2, Source #27-

0010-05

Mercury 

(Hg) Liquid 2.15E-06 11 YES

TNMilanArmyAmmu

nitionPlant

I3A-1, Source #27-

0010-12

Mercury 

(Hg) Liquid 2.15E-06 12 YES

TNMilanArmyAmmu

nitionPlant

F52L-2, Source #27-

0010-30

Mercury 

(Hg) Liquid 2.15E-06 13 YES

TNMilanArmyAmmu

nitionPlant

I4A-1, Source #27-

0010-13

Mercury 

(Hg) Liquid 2.15E-06 14 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TNMilanArmyAmmu

nitionPlant

D88L-2, Source #27-

0010-86

Mercury 

(Hg) Liquid 2.15E-06 15 YES

TNMilanArmyAmmu

nitionPlant

D88L-1, Source #27-

0010-86

Mercury 

(Hg) Liquid 2.15E-06 16 YES

TNMilanArmyAmmu

nitionPlant

D2A-1, Source #27-

0010-09

Mercury 

(Hg) Liquid 2.15E-06 17 YES

TNMilanArmyAmmu

nitionPlant

B21L-1, Source #27-

0010-28

Mercury 

(Hg) Liquid 2.15E-06 18 YES

TNMilanArmyAmmu

nitionPlant

A15L-1, Source #27-

0010-05

Mercury 

(Hg) Liquid 2.15E-06 19 YES

TNMilanArmyAmmu

nitionPlant

I5A-1, Source #27-

0010-14

Mercury 

(Hg) Liquid 2.15E-06 20 YES

TNMilanArmyAmmu

nitionPlant

K313A-1, Source 

#27-0010-83

Mercury 

(Hg) Liquid 2.15E-06 21 YES

TNMilanArmyAmmu

nitionPlant

B21L-2, Source #27-

0010-28

Mercury 

(Hg) Liquid 2.15E-06 22 NO

TNMilanArmyAmmu

nitionPlant

T116A-1, Source 

#27-0010-84

Mercury 

(Hg) Liquid 2.15E-06 23 NO

TNMilanArmyAmmu

nitionPlant

X21L-2, Source #27-

0010-29

Mercury 

(Hg) Liquid 2.15E-06 24 NO

TNMilanArmyAmmu

nitionPlant

X21L-3, Source #27-

0010-29

Mercury 

(Hg) Liquid 2.15E-06 25 NO

TNMilanArmyAmmu

nitionPlant

K300A-1, Source 

#27-0010-19

Mercury 

(Hg) Liquid 2.15E-06 26 NO

TNMilanArmyAmmu

nitionPlant

T116A-2, Source 

#27-0010-84

Mercury 

(Hg) Liquid 2.15E-06 27 NO

TNMilanArmyAmmu

nitionPlant

I6A-1, Source #27-

0010-15

Mercury 

(Hg) Liquid 2.15E-06 28 NO

TNMilanArmyAmmu

nitionPlant

S101A-2, Source 

#27-0010-21

Mercury 

(Hg) Liquid 2.15E-06 29 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TNMilanArmyAmmu

nitionPlant

S101A-1, Source 

#27-0010-21

Mercury 

(Hg) Liquid 2.15E-06 30 NO

TNMilanArmyAmmu

nitionPlant

K313A-2, Source 

#27-0010-83

Mercury 

(Hg) Liquid 2.15E-06 31 NO

TNMilanArmyAmmu

nitionPlant

K300A-2, Source 

#27-0010-19

Mercury 

(Hg) Liquid 2.15E-06 32 NO

TNMilanArmyAmmu

nitionPlant

X21L-1, Source #27-

0010-29

Mercury 

(Hg) Liquid 2.15E-06 33 NO

TNMilanArmyAmmu

nitionPlant

K102L-1, Source 

#27-0010-42

Mercury 

(Hg) Liquid 2.15E-06 34 NO

TNMilanArmyAmmu

nitionPlant

J107A-2, Source 

#27-0010-31

Mercury 

(Hg) Liquid 2.15E-06 35 NO

TNMilanArmyAmmu

nitionPlant

J107A-1, Source 

#27-0010-31

Mercury 

(Hg) Liquid 2.15E-06 36 NO

TNMilanArmyAmmu

nitionPlant

I7A-1, Source #27-

0010-16

Mercury 

(Hg) Liquid 2.15E-06 37 NO

TNMilanArmyAmmu

nitionPlant

V1L-1, Source #27-

0010-46

Mercury 

(Hg) Liquid 2.15E-06 38 NO

NCDomtar

66-25-2050 (No. 1 

Package Boiler)

Mercury 

(Hg) Liquid 5.03E-06 39 NO

TNInvistaChattanoo

ga

EU003 - Vaporizer 

#2

Mercury 

(Hg) Liquid 5.16E-06 40 NO

NCMCASCherryPoi

nt CP-4810-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 41 NO

NCMCASCherryPoi

nt CP-3916-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 42 NO

NCMCASCherryPoi

nt CP-487-BOIL-02

Mercury 

(Hg) Liquid 5.20E-06 43 NO

NCMCASCherryPoi

nt CP-487-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 44 NO

NCMCASCherryPoi

nt CP-486-BOIL-02

Mercury 

(Hg) Liquid 5.20E-06 45 NO

NCMCASCherryPoi

nt CP-486-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 46 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCMCASCherryPoi

nt CP-1782-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 47 NO

NCMCASCherryPoi

nt CP-4041-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 48 NO

NCMCASCherryPoi

nt CP-192-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 49 NO

NCMCASCherryPoi

nt CP-1799-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 50 NO

NCMCASCherryPoi

nt CP-1795-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 51 NO

NCMCASCherryPoi

nt CP-1791-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 52 NO

NCMCASCherryPoi

nt CP-1787-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 53 NO

NCMCASCherryPoi

nt CP-3919-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 54 NO

NCMCASCherryPoi

nt CP-1783-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 55 NO

NCMCASCherryPoi

nt CP-4049-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 56 NO

NCMCASCherryPoi

nt CP-1781-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 57 NO

NCMCASCherryPoi

nt CP-1780-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 58 NO

NCMCASCherryPoi

nt CP-1779-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 59 NO

NCMCASCherryPoi

nt CP-1777-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 60 NO

NCMCASCherryPoi

nt CP-152-BOIL-04

Mercury 

(Hg) Liquid 5.20E-06 61 NO

NCMCASCherryPoi

nt CP-152-BOIL-03

Mercury 

(Hg) Liquid 5.20E-06 62 NO

NCMCASCherryPoi

nt CP-1229-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 63 NO

NCMCASCherryPoi

nt CP-1786-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 64 NO

NCMCASCherryPoi

nt CP-4402-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 65 NO

NCMCASCherryPoi

nt CP-4639-BOIL-02

Mercury 

(Hg) Liquid 5.20E-06 66 NO

NCMCASCherryPoi

nt CP-4639-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 67 NO

NCMCASCherryPoi

nt CP-4576-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 68 NO

NCMCASCherryPoi

nt CP-4571-BOIL-02

Mercury 

(Hg) Liquid 5.20E-06 69 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCMCASCherryPoi

nt CP-4571-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 70 NO

NCMCASCherryPoi

nt CP-4564-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 71 NO

NCMCASCherryPoi

nt CP-248-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 72 NO

NCMCASCherryPoi

nt CP-4465-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 73 NO

NCMCASCherryPoi

nt CP-4639-BOIL-03

Mercury 

(Hg) Liquid 5.20E-06 74 NO

NCMCASCherryPoi

nt CP-4401-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 75 NO

NCMCASCherryPoi

nt CP-4390-BOIL-03

Mercury 

(Hg) Liquid 5.20E-06 76 NO

NCMCASCherryPoi

nt CP-4390-BOIL-02

Mercury 

(Hg) Liquid 5.20E-06 77 NO

NCMCASCherryPoi

nt CP-4390-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 78 NO

NCMCASCherryPoi

nt CP-4344-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 79 NO

NCMCASCherryPoi

nt CP-4298-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 80 NO

NCMCASCherryPoi

nt CP-4213-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 81 NO

NCMCASCherryPoi

nt CP-4563-BOIL-01

Mercury 

(Hg) Liquid 5.20E-06 82 NO

NCCampLejeuneM

CB C-AS-3525-15

Mercury 

(Hg) Liquid 5.21E-06 83 NO

NCCampLejeuneM

CB B-A71-H5

Mercury 

(Hg) Liquid 5.21E-06 84 NO

NCCampLejeuneM

CB A-PP-1943-H7

Mercury 

(Hg) Liquid 5.21E-06 85 NO

NCCampLejeuneM

CB C-AS-2800-12

Mercury 

(Hg) Liquid 5.21E-06 86 NO

NCCampLejeuneM

CB C-AS-1000-H21

Mercury 

(Hg) Liquid 5.21E-06 87 NO

NCCampLejeuneM

CB C-AS-1000-20

Mercury 

(Hg) Liquid 5.21E-06 88 NO

NCCampLejeuneM

CB B-BB-9-55

Mercury 

(Hg) Liquid 5.21E-06 89 NO

NCCampLejeuneM

CB B-BB-9-54

Mercury 

(Hg) Liquid 5.21E-06 90 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeuneM

CB B-BB-9-53B

Mercury 

(Hg) Liquid 5.21E-06 91 NO

NCCampLejeuneM

CB B-BB-49-52

Mercury 

(Hg) Liquid 5.21E-06 92 NO

NCCampLejeuneM

CB C-AS-4044-22

Mercury 

(Hg) Liquid 5.21E-06 93 NO

NCCampLejeuneM

CB B-A-A1-50

Mercury 

(Hg) Liquid 5.21E-06 94 NO

NCCampLejeuneM

CB C-AS-4044-23

Mercury 

(Hg) Liquid 5.21E-06 95 NO

NCCampLejeuneM

CB B-A71-49

Mercury 

(Hg) Liquid 5.21E-06 96 NO

NCCampLejeuneM

CB B-A66-H3

Mercury 

(Hg) Liquid 5.21E-06 97 NO

NCCampLejeuneM

CB B-A66-48

Mercury 

(Hg) Liquid 5.21E-06 98 NO

NCCampLejeuneM

CB A-TT-60-79

Mercury 

(Hg) Liquid 5.21E-06 99 NO

NCCampLejeuneM

CB A-TT-60-78

Mercury 

(Hg) Liquid 5.21E-06 100 NO

NCCampLejeuneM

CB A-TT-44-30

Mercury 

(Hg) Liquid 5.21E-06 101 NO

NCCampLejeuneM

CB A-TT-2457-66

Mercury 

(Hg) Liquid 5.21E-06 102 NO

NCCampLejeuneM

CB A-PP-2615-10

Mercury 

(Hg) Liquid 5.21E-06 103 NO

NCCampLejeuneM

CB C-AS-3502-08

Mercury 

(Hg) Liquid 5.21E-06 104 NO

NCCampLejeuneM

CB B-A-A47-51

Mercury 

(Hg) Liquid 5.21E-06 105 NO

NCCampLejeuneM

CB C-CG-650-84B

Mercury 

(Hg) Liquid 5.21E-06 106 NO

NCCampLejeuneM

CB C-VL-TFM204-02

Mercury 

(Hg) Liquid 5.21E-06 107 NO

NCCampLejeuneM

CB C-VL-TFM204-01

Mercury 

(Hg) Liquid 5.21E-06 108 NO

NCCampLejeuneM

CB C-VL-TFM203-02

Mercury 

(Hg) Liquid 5.21E-06 109 NO

NCCampLejeuneM

CB C-VL-TFM203-01

Mercury 

(Hg) Liquid 5.21E-06 110 NO

NCCampLejeuneM

CB C-VL-TFM104-01

Mercury 

(Hg) Liquid 5.21E-06 111 NO

NCCampLejeuneM

CB C-VL-TFM103-01

Mercury 

(Hg) Liquid 5.21E-06 112 NO

NCCampLejeuneM

CB C-TC-1500-60

Mercury 

(Hg) Liquid 5.21E-06 113 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeuneM

CB C-RR-15-47B

Mercury 

(Hg) Liquid 5.21E-06 114 NO

NCCampLejeuneM

CB C-AS-3504-09

Mercury 

(Hg) Liquid 5.21E-06 115 NO

NCCampLejeuneM

CB C-CG-650-85

Mercury 

(Hg) Liquid 5.21E-06 116 NO

NCCampLejeuneM

CB A-PP-1943-08

Mercury 

(Hg) Liquid 5.21E-06 117 NO

NCCampLejeuneM

CB C-CG-650-83B

Mercury 

(Hg) Liquid 5.21E-06 118 NO

NCCampLejeuneM

CB C-CG-480-89

Mercury 

(Hg) Liquid 5.21E-06 119 NO

NCCampLejeuneM

CB C-AS-843-14

Mercury 

(Hg) Liquid 5.21E-06 120 NO

NCCampLejeuneM

CB C-AS-840-13

Mercury 

(Hg) Liquid 5.21E-06 121 NO

NCCampLejeuneM

CB C-AS-710-03

Mercury 

(Hg) Liquid 5.21E-06 122 NO

NCCampLejeuneM

CB C-AS-705-11

Mercury 

(Hg) Liquid 5.21E-06 123 NO

NCCampLejeuneM

CB C-AS-4151-18

Mercury 

(Hg) Liquid 5.21E-06 124 NO

NCCampLejeuneM

CB C-AS-4151-17A

Mercury 

(Hg) Liquid 5.21E-06 125 NO

NCCampLejeuneM

CB C-AS-4151-16

Mercury 

(Hg) Liquid 5.21E-06 126 NO

NCCampLejeuneM

CB C-RR-15-46B

Mercury 

(Hg) Liquid 5.21E-06 127 NO

NCCampLejeuneM

CB A-BM-890-H9

Mercury 

(Hg) Liquid 5.21E-06 128 NO

NCCampLejeuneM

CB A-PP-2615-09

Mercury 

(Hg) Liquid 5.21E-06 129 NO

NCCampLejeuneM

CB A-HP-2027-H15

Mercury 

(Hg) Liquid 5.21E-06 130 NO

NCCampLejeuneM

CB A-HP-2027-H14

Mercury 

(Hg) Liquid 5.21E-06 131 NO

NCCampLejeuneM

CB A-HP-2027-H13

Mercury 

(Hg) Liquid 5.21E-06 132 NO

NCCampLejeuneM

CB A-HP-2027-21

Mercury 

(Hg) Liquid 5.21E-06 133 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeuneM

CB A-HP-2027-20

Mercury 

(Hg) Liquid 5.21E-06 134 NO

NCCampLejeuneM

CB A-HP-1700-05

Mercury 

(Hg) Liquid 5.21E-06 135 NO

NCCampLejeuneM

CB A-FC-989-31

Mercury 

(Hg) Liquid 5.21E-06 136 NO

NCCampLejeuneM

CB A-HP-40-75

Mercury 

(Hg) Liquid 5.21E-06 137 NO

NCCampLejeuneM

CB A-FC-260-90

Mercury 

(Hg) Liquid 5.21E-06 138 NO

NCCampLejeuneM

CB A-HP-40-76

Mercury 

(Hg) Liquid 5.21E-06 139 NO

NCCampLejeuneM

CB A-BM-890-H10

Mercury 

(Hg) Liquid 5.21E-06 140 NO

NCCampLejeuneM

CB A-BM-890-15

Mercury 

(Hg) Liquid 5.21E-06 141 NO

NCCampLejeuneM

CB A-BM-890-14

Mercury 

(Hg) Liquid 5.21E-06 142 NO

NCCampLejeuneM

CB A-BM-835-07

Mercury 

(Hg) Liquid 5.21E-06 143 NO

NCCampLejeuneM

CB A-BM-835-06

Mercury 

(Hg) Liquid 5.21E-06 144 NO

NCCampLejeuneM

CB A-BM-825-H1

Mercury 

(Hg) Liquid 5.21E-06 145 NO

NCCampLejeuneM

CB A-BM-825-13

Mercury 

(Hg) Liquid 5.21E-06 146 NO

NCCampLejeuneM

CB A-BM-825-12

Mercury 

(Hg) Liquid 5.21E-06 147 NO

NCCampLejeuneM

CB A-BM-5400-81

Mercury 

(Hg) Liquid 5.21E-06 148 NO

NCCampLejeuneM

CB A-FC-440-87

Mercury 

(Hg) Liquid 5.21E-06 149 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeuneM

CB A-MP-625-72

Mercury 

(Hg) Liquid 5.21E-06 150 NO

NCCampLejeuneM

CB A-NH-121-H1

Mercury 

(Hg) Liquid 5.21E-06 151 NO

NCCampLejeuneM

CB A-NH-121-01

Mercury 

(Hg) Liquid 5.21E-06 152 NO

NCCampLejeuneM

CB A-NH-120-H4

Mercury 

(Hg) Liquid 5.21E-06 153 NO

NCCampLejeuneM

CB A-NH-120-04

Mercury 

(Hg) Liquid 5.21E-06 154 NO

NCCampLejeuneM

CB A-NH-118-03

Mercury 

(Hg) Liquid 5.21E-06 155 NO

NCCampLejeuneM

CB A-NH-100-05

Mercury 

(Hg) Liquid 5.21E-06 156 NO

NCCampLejeuneM

CB A-NH-100-02

Mercury 

(Hg) Liquid 5.21E-06 157 NO

NCCampLejeuneM

CB A-NH-100-01

Mercury 

(Hg) Liquid 5.21E-06 158 NO

NCCampLejeuneM

CB A-HP-2027-H16

Mercury 

(Hg) Liquid 5.21E-06 159 NO

NCCampLejeuneM

CB A-MP-625-73

Mercury 

(Hg) Liquid 5.21E-06 160 NO

NCCampLejeuneM

CB A-BM-5400-80

Mercury 

(Hg) Liquid 5.21E-06 161 NO

NCCampLejeuneM

CB A-MP-230-40

Mercury 

(Hg) Liquid 5.21E-06 162 NO

NCCampLejeuneM

CB A-MP-230-39

Mercury 

(Hg) Liquid 5.21E-06 163 NO

NCCampLejeuneM

CB A-MP-230-38

Mercury 

(Hg) Liquid 5.21E-06 164 NO

NCCampLejeuneM

CB A-MG-SH8-58

Mercury 

(Hg) Liquid 5.21E-06 165 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 1-Hg Floor

FacilityID

CombustorID_com

mon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeuneM

CB A-LCH-4022-19

Mercury 

(Hg) Liquid 5.21E-06 166 NO

NCCampLejeuneM

CB A-LCH-4014-17

Mercury 

(Hg) Liquid 5.21E-06 167 NO

NCCampLejeuneM

CB A-HP-989-31

Mercury 

(Hg) Liquid 5.21E-06 168 NO

NCCampLejeuneM

CB A-HP-738-59

Mercury 

(Hg) Liquid 5.21E-06 169 NO

NCCampLejeuneM

CB A-HP-670-88

Mercury 

(Hg) Liquid 5.21E-06 170 NO

NCCampLejeuneM

CB A-HP-500-86

Mercury 

(Hg) Liquid 5.21E-06 171 NO

NCCampLejeuneM

CB A-MP-625-74

Mercury 

(Hg) Liquid 5.21E-06 172 NO

SCGPChemRussell

ville FO Boiler

Mercury 

(Hg) Liquid 4.90E-05 173 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ARPotlatchFore

stWarren Wellons Boiler

Hydrogen 

Chloride 

(HCl) Biomass 3.69E-06 1 YES

WABoisePaper

Wallula Hog Fuel Boiler

Hydrogen 

Chloride 

(HCl) Biomass 8.93E-05 2 YES

FLSugarCaneG

rowersCoop Boiler No. 8

Hydrogen 

Chloride 

(HCl) Biomass 1.99E-04 3 YES

ARAnthonyFore

stProducts SN-12

Hydrogen 

Chloride 

(HCl) Biomass 2.00E-04 4 YES

WAGraysHarbo

rPaper

No. 6 Boiler 

(EU2)

Hydrogen 

Chloride 

(HCl) Biomass 2.00E-04 5 YES

FLUSSugarCor

p Boiler No. 4

Hydrogen 

Chloride 

(HCl) Biomass 2.02E-04 6 YES

MSHoodWayne

sboro

AA-001 (WoodFired Boiler)

Hydrogen 

Chloride 

(HCl) Biomass 2.11E-04 7 YES

NCGPRoxboro

ES-1 Wood 

fired Boiler

Hydrogen 

Chloride 

(HCl) Biomass 2.17E-04 8 NO

ORWeyerhaeus

erCoWarrenton

LumberMill 3-HFB

Hydrogen 

Chloride 

(HCl) Biomass 2.25E-04 9 NO

NCLPRoaringRi

ver Boiler #2

Hydrogen 

Chloride 

(HCl) Biomass 2.53E-04 10 NO

MSHankinsLum

ber

Boiler #1 (AA001)

Hydrogen 

Chloride 

(HCl) Biomass 2.60E-04 11 NO

WAWeyerhaeu

ser_Raymond

Hog Fuel Boiler 

EU1

Hydrogen 

Chloride 

(HCl) Biomass 2.67E-04 12 NO

ORRoseburgCo

quille Boiler 1

Hydrogen 

Chloride 

(HCl) Biomass 3.40E-04 13 NO

NDCargillWestF

argo

Foster Wheeler 

Boiler (EU43)

Hydrogen 

Chloride 

(HCl) Biomass 3.56E-04 14 NO

GARayonierJes

upMill PB01

Hydrogen 

Chloride 

(HCl) Biomass 3.67E-04 15 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNDESPHans

ONyman EU007

Hydrogen 

Chloride 

(HCl) Biomass 3.70E-04 16 NO

IDMoyieSprings 

Lumber420 HFB1

Hydrogen 

Chloride 

(HCl) Biomass 3.83E-04 17 NO

MNAndersonCo

rpBayport

Boiler 11 

EU620

Hydrogen 

Chloride 

(HCl) Biomass 4.00E-04 18 NO

MNAndersonCo

rpBayport

Boiler 12 

EU621

Hydrogen 

Chloride 

(HCl) Biomass 4.00E-04 19 NO

MSWeyerhaeus

erBruce

AA-002 No. 2 

Boiler

Hydrogen 

Chloride 

(HCl) Biomass 5.07E-04 20 NO

FLUSSugarCor

p Boiler No. 7

Hydrogen 

Chloride 

(HCl) Biomass 5.37E-04 21 NO

GAGPCellulose

Brunswick

U700 -- No. 4 

Power Boiler

Hydrogen 

Chloride 

(HCl) Biomass 5.53E-04 22 NO

ORRoseburgRi

ddle2 Boiler #2

Hydrogen 

Chloride 

(HCl) Biomass 5.67E-04 23 NO

ORRoseburgFo

restDillard Boiler #6

Hydrogen 

Chloride 

(HCl) Biomass 7.90E-04 24 NO

SCNewSouthC

amden WWB1

Hydrogen 

Chloride 

(HCl) Biomass 8.67E-04 25 NO

ORRoseburgFo

restDillard Boiler #1

Hydrogen 

Chloride 

(HCl) Biomass 9.39E-04 26 NO

ARWeyerhaeus

erDierksMill SN-45

Hydrogen 

Chloride 

(HCl) Biomass 1.00E-03 27 NO

GARayonierJes

upMill PB03

Hydrogen 

Chloride 

(HCl) Biomass 1.00E-03 28 NO

MIWhitePineEle

ctric IBW Boiler

Hydrogen 

Chloride 

(HCl) Biomass 1.00E-03 29 NO

MSGPNewAug

usta

AA-015 Power 

Boiler

Hydrogen 

Chloride 

(HCl) Biomass 1.00E-03 30 NO

HIPuuneneSug

arMill Boiler 1

Hydrogen 

Chloride 

(HCl) Biomass 1.03E-03 31 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

HIPuuneneSug

arMill Boiler 2

Hydrogen 

Chloride 

(HCl) Biomass 1.03E-03 32 NO

SCNewSouthC

oConway WWB1

Hydrogen 

Chloride 

(HCl) Biomass 1.20E-03 33 NO

GAGPWarmSpr

ings

EU600 Wood 

Fuel Boiler

Hydrogen 

Chloride 

(HCl) Biomass 1.20E-03 34 NO

SCSmurfitStone

Unit 15: Boiler 

#3

Hydrogen 

Chloride 

(HCl) Biomass 1.27E-03 35 NO

NYIntlPaperTic

onderoga PB1

Hydrogen 

Chloride 

(HCl) Biomass 1.32E-03 36 NO

ARGBPMorrilto

n SN-04

Hydrogen 

Chloride 

(HCl) Biomass 1.34E-03 37 NO

ORRoseburgRi

ddle2 Boiler #1

Hydrogen 

Chloride 

(HCl) Biomass 1.40E-03 38 NO

ORRoseburgFo

restDillard Boiler #2

Hydrogen 

Chloride 

(HCl) Biomass 2.24E-03 39 NO

FLUSSugarCor

p Boiler No. 8

Hydrogen 

Chloride 

(HCl) Biomass 2.30E-03 40 NO

GARayonierJes

upMill PB02

Hydrogen 

Chloride 

(HCl) Biomass 2.33E-03 41 NO

NCLPRoaringRi

ver Boiler #3

Hydrogen 

Chloride 

(HCl) Biomass 3.63E-03 42 NO

WAGraysHarbo

rPaper

No. 8 Boiler 

(EU1)

Hydrogen 

Chloride 

(HCl) Biomass 3.67E-03 43 NO

FLSugarCaneG

rowersCoop Boiler No. 2

Hydrogen 

Chloride 

(HCl) Biomass 3.83E-03 44 NO

ALIPCourtland

No. 1 

Combination 

Boiler / 

11CU101

Hydrogen 

Chloride 

(HCl) Biomass 4.18E-03 45 NO

ARPotlatchFore

stPrescott

McBurney 

Boiler

Hydrogen 

Chloride 

(HCl) Biomass 4.27E-03 46 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ORRosboroSpri

ngfield DV 01.1

Hydrogen 

Chloride 

(HCl) Biomass 5.60E-03 47 NO

FLSmurfitStone 5PB

Hydrogen 

Chloride 

(HCl) Biomass 6.25E-03 48 NO

KYWeyerhaeus

erEKY MP 01-01

Hydrogen 

Chloride 

(HCl) Biomass 1.38E-02 49 NO

KYWeyerhaeus

erEKY MP 01-02

Hydrogen 

Chloride 

(HCl) Biomass 1.38E-02 50 NO

KYWeyerhaeus

erEKY MP 01-03

Hydrogen 

Chloride 

(HCl) Biomass 1.38E-02 51 NO

INAlcoaWarrick Unit #3

Hydrogen 

Chloride 

(HCl) Coal 1.50E-05 1 YES

IDTASCOPaul Erie City Boiler

Hydrogen 

Chloride 

(HCl) Coal 3.85E-05 2 YES

INAlcoaWarrick Unit #2

Hydrogen 

Chloride 

(HCl) Coal 5.91E-05 3 YES

IARoquetteAme

rica

Circulating 

Fluidized Bed 

Boiler (121)

Hydrogen 

Chloride 

(HCl) Coal 6.18E-05 4 YES

TNEastman_N

O_CBIDATA Boiler 30

Hydrogen 

Chloride 

(HCl) Coal 7.23E-05 5 YES

AZCatalystPape

rSnowflake

Power Boiler #2 

Coal

Hydrogen 

Chloride 

(HCl) Coal 1.16E-04 6 YES

MOJamesRiver

PowerStation Unit 1

Hydrogen 

Chloride 

(HCl) Coal 2.12E-04 7 YES

MOJamesRiver

PowerStation Unit 2

Hydrogen 

Chloride 

(HCl) Coal 2.12E-04 8 YES

ALIPCourtland

No.2 

Combination 

Boiler / 

11CU201

Hydrogen 

Chloride 

(HCl) Coal 2.82E-04 9 YES

IDTASCOPaul

Babcock and 

Wilcox (B&W) 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 3.00E-04 10 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NDMinnDakFar

mers

Babcock and 

Wilcox Boiler 

#5

Hydrogen 

Chloride 

(HCl) Coal 3.64E-04 11 YES

IAArchersDaniel

sMidlandDesMo

ines Asea Boiler #1

Hydrogen 

Chloride 

(HCl) Coal 3.88E-04 12 YES

VAUniversityofV

irginia 7103-1-01R

Hydrogen 

Chloride 

(HCl) Coal 5.69E-04 13 YES

WINewPageBir

on B24

Hydrogen 

Chloride 

(HCl) Coal 5.87E-04 14 YES

MICityofEscana

ba EUBOILER#1

Hydrogen 

Chloride 

(HCl) Coal 6.00E-04 15 YES

VASmurfitStone

Westpt PB08

Hydrogen 

Chloride 

(HCl) Coal 6.69E-04 16 YES

TNEastman_N

O_CBIDATA Boiler 31

Hydrogen 

Chloride 

(HCl) Coal 7.00E-04 17 YES

WINewPageWisconsinRapid

s

Power Boiler 1 - 

B21

Hydrogen 

Chloride 

(HCl) Coal 8.00E-04 18 YES

PADomtarJohn

sonburg #81 Coal Boiler

Hydrogen 

Chloride 

(HCl) Coal 8.33E-04 19 YES

PADomtarJohn

sonburg #82 Coal Boiler

Hydrogen 

Chloride 

(HCl) Coal 8.33E-04 20 YES

IDTASCONamp

a

Babcock and 

Wilcox (B&W) 

#1

Hydrogen 

Chloride 

(HCl) Coal 9.00E-04 21 YES

IDTASCONamp

a

Babcock and 

Wilcox (B&W) 

#2

Hydrogen 

Chloride 

(HCl) Coal 9.00E-04 22 YES

WINewPageWisconsinRapid

s

Power Boiler 2 - 

B20

Hydrogen 

Chloride 

(HCl) Coal 9.00E-04 23 YES

IAMuscatinePo

werandWater Unit 7

Hydrogen 

Chloride 

(HCl) Coal 1.14E-03 24 YES

IDAmalgamated

SugarCoTwinFa

lls S-B2

Hydrogen 

Chloride 

(HCl) Coal 1.33E-03 25 YES

OHPainesvilleM

unicipalElectric B004

Hydrogen 

Chloride 

(HCl) Coal 1.33E-03 26 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MIPharma&Upj

ohn1180 Boiler 3

Hydrogen 

Chloride 

(HCl) Coal 1.45E-03 27 YES

WYGeneralChe

mical

GR-2-L (C 

BOILER)

Hydrogen 

Chloride 

(HCl) Coal 1.80E-03 28 YES

TNEastman_N

O_CBIDATA Boiler 27

Hydrogen 

Chloride 

(HCl) Coal 1.87E-03 29 YES

ILPrairiePowerP

earl B1

Hydrogen 

Chloride 

(HCl) Coal 1.93E-03 30 YES

WYGeneralChe

mical

GR-3-W (D 

BOILER)

Hydrogen 

Chloride 

(HCl) Coal 1.97E-03 31 YES

MNAmericanCr

ystalMoorhead Boiler 3

Hydrogen 

Chloride 

(HCl) Coal 2.00E-03 32 YES

OHPainesvilleM

unicipalElectric B003

Hydrogen 

Chloride 

(HCl) Coal 2.00E-03 33 YES

INSABICInnova

tivePlastics

09-002 Erie 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 2.65E-03 34 YES

INSABICInnova

tivePlastics

09-002 Lasker 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 2.65E-03 35 YES

WINewPageWhiting B24

Hydrogen 

Chloride 

(HCl) Coal 2.73E-03 36 YES

AKDoyonUtilitie

s_AK 7

Hydrogen 

Chloride 

(HCl) Coal 3.03E-03 37 NO

AKDoyonUtilitie

s_AK 4

Hydrogen 

Chloride 

(HCl) Coal 3.27E-03 38 NO

NCMCASCherr

yPoint

CP-152-BOIL02

Hydrogen 

Chloride 

(HCl) Coal 3.67E-03 39 NO

GAGPSRMRiin

con EU BO01

Hydrogen 

Chloride 

(HCl) Coal 3.97E-03 40 NO

OHDukeEnergy

GenerationCinci

nnati

B022 (Boiler #4, 

IG-4A)

Hydrogen 

Chloride 

(HCl) Coal 4.00E-03 41 NO

OHOrrvilleUtiliti

es B006

Hydrogen 

Chloride 

(HCl) Coal 4.00E-03 42 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

INPurdueUniver

isity Boiler 5

Hydrogen 

Chloride 

(HCl) Coal 4.33E-03 43 NO

OHOrrvilleUtiliti

es B001

Hydrogen 

Chloride 

(HCl) Coal 4.67E-03 44 NO

OHOrrvilleUtiliti

es B004

Hydrogen 

Chloride 

(HCl) Coal 4.67E-03 45 NO

OHPainesvilleM

unicipalElectric B001

Hydrogen 

Chloride 

(HCl) Coal 5.67E-03 46 NO

INTateLyleLafa

yetteSouth LA-45

Hydrogen 

Chloride 

(HCl) Coal 6.47E-03 47 NO

NCBlueRidgeP

aper G11040

Hydrogen 

Chloride 

(HCl) Coal 6.93E-03 48 NO

OHAkronTherm

alEnergy

Boiler #32 

(B001)

Hydrogen 

Chloride 

(HCl) Coal 7.03E-03 49 NO

GAIPSavannah

No. 13 Power 

Boiler - PB13

Hydrogen 

Chloride 

(HCl) Coal 7.17E-03 50 NO

INTateLyleSaga

more 31B1

Hydrogen 

Chloride 

(HCl) Coal 7.27E-03 51 NO

SCGaley&Lord 1EB1

Hydrogen 

Chloride 

(HCl) Coal 7.47E-03 52 NO

SCGaley&Lord 1FB1

Hydrogen 

Chloride 

(HCl) Coal 7.47E-03 53 NO

OHShelbyMuni

LightPlant B008

Hydrogen 

Chloride 

(HCl) Coal 8.00E-03 54 NO

TNBowaterNew

sprint

Power Boiler 

No. 3

Hydrogen 

Chloride 

(HCl) Coal 8.00E-03 55 NO

TNEastman_N

O_CBIDATA Boiler 25

Hydrogen 

Chloride 

(HCl) Coal 8.00E-03 56 NO

ALGeorgiaPacifi

cNaheola Z015 - CB1

Hydrogen 

Chloride 

(HCl) Coal 8.30E-03 57 NO

NCEIDuPontKin

ston ES6022B

Hydrogen 

Chloride 

(HCl) Coal 8.57E-03 58 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TNBowaterNew

sprint

Power Boiler 

No. 1

Hydrogen 

Chloride 

(HCl) Coal 8.67E-03 59 NO

NCMCASCherr

yPoint

CP-152-BOIL01

Hydrogen 

Chloride 

(HCl) Coal 9.40E-03 60 NO

NCMillerCoors

ES-2 Coal/No. 2 

& 6 Fuel Oil 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.00E-02 61 NO

WIWausauRhin

e B26

Hydrogen 

Chloride 

(HCl) Coal 1.03E-02 62 NO

ALCargillDecatur Keeler (S-407)

Hydrogen 

Chloride 

(HCl) Coal 1.07E-02 63 NO

MIHollandBPW Unit 3

Hydrogen 

Chloride 

(HCl) Coal 1.07E-02 64 NO

OHShelbyMuni

LightPlant B007

Hydrogen 

Chloride 

(HCl) Coal 1.07E-02 65 NO

TNOakRidgeY12 Boiler/Unit 31

Hydrogen 

Chloride 

(HCl) Coal 1.07E-02 66 NO

NCEIDuPontKin

ston ES6022A

Hydrogen 

Chloride 

(HCl) Coal 1.10E-02 67 NO

GAInternational

PaperAugustaM

ills PB2A

Hydrogen 

Chloride 

(HCl) Coal 1.13E-02 68 NO

IDAmalgamated

SugarCoTwinFa

lls S-B1

Hydrogen 

Chloride 

(HCl) Coal 1.17E-02 69 NO

OHShelbyMuni

LightPlant B006

Hydrogen 

Chloride 

(HCl) Coal 1.20E-02 70 NO

NCNC_DukeUn

iversity_Durham 7754-01

Hydrogen 

Chloride 

(HCl) Coal 1.20E-02 71 NO

OKGPMuskoge

eMill B-2

Hydrogen 

Chloride 

(HCl) Coal 1.23E-02 72 NO

NJVinelandMun

iElectricHowardDown Unit 10

Hydrogen 

Chloride 

(HCl) Coal 1.24E-02 73 NO

NCUNCCogen ES-001

Hydrogen 

Chloride 

(HCl) Coal 1.28E-02 74 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VAGPBigIsland

2703

PWR04 - No. 4 

Power Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.31E-02 75 NO

VAGPJarrattFib

erboard

EP-15 No. 3 

Keeler Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.37E-02 76 NO

INSABICInnova

tivePlastics

01-001 BW1 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.47E-02 77 NO

INSABICInnova

tivePlastics

01-001 BW2 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.47E-02 78 NO

OHMedicalCent

erCo1915 B003

Hydrogen 

Chloride 

(HCl) Coal 1.65E-02 79 NO

OHMedicalCent

erCo1915 B004

Hydrogen 

Chloride 

(HCl) Coal 1.65E-02 80 NO

NCCampLejeun

eMCB A-HP-1700-03

Hydrogen 

Chloride 

(HCl) Coal 1.67E-02 81 NO

NCCampLejeun

eMCB A-HP-1700-04

Hydrogen 

Chloride 

(HCl) Coal 1.67E-02 82 NO

VAINVISTAWa

ynesboro

2-205 (B#2) 

Boiler #2

Hydrogen 

Chloride 

(HCl) Coal 1.73E-02 83 NO

MOAnheuserBu

sch Boiler 5

Hydrogen 

Chloride 

(HCl) Coal 1.77E-02 84 NO

ALGeorgiaPacifi

cNaheola Z016 - CB2

Hydrogen 

Chloride 

(HCl) Coal 1.88E-02 85 NO

MIHollandBPW Unit 4

Hydrogen 

Chloride 

(HCl) Coal 2.00E-02 86 NO

TNViskase Boiler 1

Hydrogen 

Chloride 

(HCl) Coal 2.00E-02 87 NO

TNViskase Boiler 2

Hydrogen 

Chloride 

(HCl) Coal 2.00E-02 88 NO

IAJohnDeereDu

buque Boiler 4

Hydrogen 

Chloride 

(HCl) Coal 2.15E-02 89 NO

IAJohnDeereDu

buque Boiler 1

Hydrogen 

Chloride 

(HCl) Coal 2.17E-02 90 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IAJohnDeereDu

buque Boiler 3

Hydrogen 

Chloride 

(HCl) Coal 2.17E-02 91 NO

IAUofIowa EP7 Boiler 11

Hydrogen 

Chloride 

(HCl) Coal 2.30E-02 92 NO

OHMortonSaltR

ittman

B003 - CoalFired Boiler #1

Hydrogen 

Chloride 

(HCl) Coal 2.30E-02 93 NO

MOTrigenKans

asCity Boiler 6

Hydrogen 

Chloride 

(HCl) Coal 2.35E-02 94 NO

NCMillerCoors

ES-1 Coal/No. 2 

& 6 Fuel Oil 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 2.37E-02 95 NO

WVBayerInstitut

e Boiler #10

Hydrogen 

Chloride 

(HCl) Coal 2.37E-02 96 NO

NCTysonHarmo

ny TYS-ES-21

Hydrogen 

Chloride 

(HCl) Coal 2.40E-02 97 NO

IAADMCornPro

cessingCR EU-501B

Hydrogen 

Chloride 

(HCl) Coal 2.53E-02 98 NO

MOUofMissouri Boiler 11

Hydrogen 

Chloride 

(HCl) Coal 2.58E-02 99 NO

OKGPMuskoge

eMill B-3

Hydrogen 

Chloride 

(HCl) Coal 3.03E-02 100 NO

WIGPGreenBay

2818

B26 - Stoker 

Boiler #6

Hydrogen 

Chloride 

(HCl) Coal 3.16E-02 101 NO

WIGPGreenBay

2818

B27 - Cyclone 

Boiler #7

Hydrogen 

Chloride 

(HCl) Coal 3.16E-02 102 NO

WIGPGreenBay

2818

B28 - Stoker 

Boiler #8

Hydrogen 

Chloride 

(HCl) Coal 3.16E-02 103 NO

MNWausauPap

er-Brainerd EU 003

Hydrogen 

Chloride 

(HCl) Coal 3.20E-02 104 NO

MDNewPageLuke No. 25

Hydrogen 

Chloride 

(HCl) Coal 3.23E-02 105 NO

OKGPMuskoge

eMill B-4

Hydrogen 

Chloride 

(HCl) Coal 3.23E-02 106 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILBungeDanvill

e CFB Boiler

Hydrogen 

Chloride 

(HCl) Coal 3.28E-02 107 NO

MNDESPHans

ONyman EU003

Hydrogen 

Chloride 

(HCl) Coal 3.30E-02 108 NO

WVBayerInstitut

e Boiler #11

Hydrogen 

Chloride 

(HCl) Coal 3.33E-02 109 NO

IACentralIAPow

er

EP1 Unit 1 PC 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 3.35E-02 110 NO

MNWausauPap

er-Brainerd EU 002

Hydrogen 

Chloride 

(HCl) Coal 3.39E-02 111 NO

GACaraustar CB01

Hydrogen 

Chloride 

(HCl) Coal 3.53E-02 112 NO

MDDeptofNavy

SupportFacilityI

ndianHead

PTO - 873 - E3 

(3-0006) (Boiler 

3)

Hydrogen 

Chloride 

(HCl) Coal 3.65E-02 113 NO

MOTrigenKans

asCity Boiler 8

Hydrogen 

Chloride 

(HCl) Coal 3.74E-02 114 NO

NCUNCCogen ES-002

Hydrogen 

Chloride 

(HCl) Coal 3.83E-02 115 NO

NCBlueRidgeP

aper G11039

Hydrogen 

Chloride 

(HCl) Coal 4.10E-02 116 NO

MDDeptofNavy

SupportFacilityI

ndianHead

PTO - 873 - E2 

(3-0005) (Boiler 

2)

Hydrogen 

Chloride 

(HCl) Coal 4.39E-02 117 NO

WVPPGMartins

ville R011-Boiler 3

Hydrogen 

Chloride 

(HCl) Coal 4.67E-02 118 NO

MNWausauPap

er-Brainerd EU 004

Hydrogen 

Chloride 

(HCl) Coal 4.77E-02 119 NO

OHUSEnrichme

ntCorpPiketon

X-600 Boiler 

No. 1

Hydrogen 

Chloride 

(HCl) Coal 4.83E-02 120 NO

MOIPLBlueVall

ey Unit 1

Hydrogen 

Chloride 

(HCl) Coal 4.97E-02 121 NO

IACargillEddyvill

e 1.001

Hydrogen 

Chloride 

(HCl) Coal 5.00E-02 122 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IACargillEddyvill

e 1.002

Hydrogen 

Chloride 

(HCl) Coal 5.00E-02 123 NO

IACargillEddyvill

e 1.039

Hydrogen 

Chloride 

(HCl) Coal 5.00E-02 124 NO

ILRockIslandAr

senal Boiler #4

Hydrogen 

Chloride 

(HCl) Coal 5.08E-02 125 NO

VADukeEnergy

Narrows Boiler #1

Hydrogen 

Chloride 

(HCl) Coal 5.19E-02 126 NO

NYCornellUnive

rsity B8

Hydrogen 

Chloride 

(HCl) Coal 5.27E-02 127 NO

IAJohnDeereDu

buque Boiler 2

Hydrogen 

Chloride 

(HCl) Coal 5.28E-02 128 NO

PABellefieldPla

nt Boiler 3

Hydrogen 

Chloride 

(HCl) Coal 5.30E-02 129 NO

MDDeptofNavy

SupportFacilityI

ndianHead

PTO - 873 - E1 

(3-0004) (Boiler 

1)

Hydrogen 

Chloride 

(HCl) Coal 5.48E-02 130 NO

MOIPLBlueVall

ey Unit 2

Hydrogen 

Chloride 

(HCl) Coal 5.53E-02 131 NO

WIWausau

# 6 Power 

Boiler (B20)

Hydrogen 

Chloride 

(HCl) Coal 5.60E-02 132 NO

MOAnheuserBu

sch Boiler 1

Hydrogen 

Chloride 

(HCl) Coal 5.95E-02 133 NO

TNDuPontOldHi

ckoryPlant #24 Boiler

Hydrogen 

Chloride 

(HCl) Coal 6.00E-02 134 NO

NCBlueRidgeP

aper G11037

Hydrogen 

Chloride 

(HCl) Coal 6.03E-02 135 NO

NCBlueRidgeP

aper G11038

Hydrogen 

Chloride 

(HCl) Coal 6.03E-02 136 NO

GACargillGainesville B001

Hydrogen 

Chloride 

(HCl) Coal 6.07E-02 137 NO

OHUSEnrichme

ntCorpPiketon

X-600 Boiler 

No. 2

Hydrogen 

Chloride 

(HCl) Coal 6.07E-02 138 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WIWausau

# 5 Power 

Boiler (B24)

Hydrogen 

Chloride 

(HCl) Coal 6.13E-02 139 NO

TNDuPontOldHi

ckoryPlant #20 Boiler

Hydrogen 

Chloride 

(HCl) Coal 6.17E-02 140 NO

PAPHGlatfelter PB4

Hydrogen 

Chloride 

(HCl) Coal 6.20E-02 141 NO

PAPHGlatfelter PB3

Hydrogen 

Chloride 

(HCl) Coal 6.20E-02 142 NO

OHUSEnrichme

ntCorpPiketon

X-600 Boiler 

No. 3

Hydrogen 

Chloride 

(HCl) Coal 6.20E-02 143 NO

TNInvistaChatta

nooga

EU002 - Boiler 

#3

Hydrogen 

Chloride 

(HCl) Coal 6.20E-02 144 NO

PAPHGlatfelter PB1

Hydrogen 

Chloride 

(HCl) Coal 6.20E-02 145 NO

VAPhilipMorris

MC PC

Hydrogen 

Chloride 

(HCl) Coal 6.28E-02 146 NO

NYCornellUnive

rsity B1

Hydrogen 

Chloride 

(HCl) Coal 6.40E-02 147 NO

NCCampLejeun

eMCB A-HP-1700-01

Hydrogen 

Chloride 

(HCl) Coal 6.47E-02 148 NO

NCCampLejeun

eMCB A-HP-1700-02

Hydrogen 

Chloride 

(HCl) Coal 6.47E-02 149 NO

WVDuPontWas

hingtonWorks P01

Hydrogen 

Chloride 

(HCl) Coal 6.53E-02 150 NO

ILAbbottAbbott

Park Unit 5AP

Hydrogen 

Chloride 

(HCl) Coal 6.54E-02 151 NO

WVDuPontWas

hingtonWorks P02

Hydrogen 

Chloride 

(HCl) Coal 6.57E-02 152 NO

MOMarshallMu

nicipal Unit # 4

Hydrogen 

Chloride 

(HCl) Coal 6.71E-02 153 NO

VAINVISTAWa

ynesboro

2-205 (B#1) 

Boiler #1

Hydrogen 

Chloride 

(HCl) Coal 6.75E-02 154 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILRockIslandAr

senal

NBN 12602 

(Boiler #1)

Hydrogen 

Chloride 

(HCl) Coal 6.85E-02 155 NO

MOColumbiaPo

werPlant Boiler Unit 6

Hydrogen 

Chloride 

(HCl) Coal 7.10E-02 156 NO

MOColumbiaPo

werPlant Boiler Unit 7

Hydrogen 

Chloride 

(HCl) Coal 7.10E-02 157 NO

VAPhilipMorrisP

ark500 B2

Hydrogen 

Chloride 

(HCl) Coal 7.20E-02 158 NO

IAIAStateUnivP

owerPlant B5

Hydrogen 

Chloride 

(HCl) Coal 7.34E-02 159 NO

MITBSimonPow

erPlant Unit 4

Hydrogen 

Chloride 

(HCl) Coal 7.46E-02 160 NO

IAUofNorthernIo

wa Boiler #3

Hydrogen 

Chloride 

(HCl) Coal 7.53E-02 161 NO

VARadfordArmy

AmmunitionPla

nt Boiler No. 4

Hydrogen 

Chloride 

(HCl) Coal 7.57E-02 162 NO

WINewPageBir

on B23

Hydrogen 

Chloride 

(HCl) Coal 7.62E-02 163 NO

MSDuPontDeLi

sle1342

AF-101A (BLR1342)

Hydrogen 

Chloride 

(HCl) Coal 7.67E-02 164 NO

MSDuPontDeLi

sle1342

AF-101B (BLR1342)

Hydrogen 

Chloride 

(HCl) Coal 7.67E-02 165 NO

IAIAStateUnivP

owerPlant B4

Hydrogen 

Chloride 

(HCl) Coal 7.70E-02 166 NO

WIDairylandPo

wer-Alma Alma 1

Hydrogen 

Chloride 

(HCl) Coal 7.72E-02 167 NO

WIDairylandPo

wer-Alma Alma 2

Hydrogen 

Chloride 

(HCl) Coal 7.72E-02 168 NO

WIDairylandPo

wer-Alma Alma 3

Hydrogen 

Chloride 

(HCl) Coal 7.72E-02 169 NO

WVDuPontWas

hingtonWorks P04

Hydrogen 

Chloride 

(HCl) Coal 7.83E-02 170 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IAIAStateUnivP

owerPlant B1

Hydrogen 

Chloride 

(HCl) Coal 7.84E-02 171 NO

OHMortonSaltR

ittman

B002 - CoalFired Boiler #2

Hydrogen 

Chloride 

(HCl) Coal 7.90E-02 172 NO

MITBSimonPow

erPlant Unit 3

Hydrogen 

Chloride 

(HCl) Coal 7.95E-02 173 NO

MNRochesterUt

ilities EU003

Hydrogen 

Chloride 

(HCl) Coal 7.97E-02 174 NO

INNotreDame B-4

Hydrogen 

Chloride 

(HCl) Coal 8.07E-02 175 NO

ILRockIslandAr

senal

NBN 12888 

(Boiler #2)

Hydrogen 

Chloride 

(HCl) Coal 8.15E-02 176 NO

MOAnheuserBu

sch Boiler 8

Hydrogen 

Chloride 

(HCl) Coal 8.24E-02 177 NO

VAPhilipMorrisP

ark500 B3

Hydrogen 

Chloride 

(HCl) Coal 8.31E-02 178 NO

ILRockIslandAr

senal

NBN 3059 

(Boiler #3)

Hydrogen 

Chloride 

(HCl) Coal 8.38E-02 179 NO

MNDESPHans

ONyman EU002

Hydrogen 

Chloride 

(HCl) Coal 8.40E-02 180 NO

MNRochesterUt

ilities EU001

Hydrogen 

Chloride 

(HCl) Coal 8.43E-02 181 NO

WVDuPontWas

hingtonWorks P06

Hydrogen 

Chloride 

(HCl) Coal 8.73E-02 182 NO

WIThilmanyPap

ersNicoletMill B23

Hydrogen 

Chloride 

(HCl) Coal 8.80E-02 183 NO

WIThilmanyPap

ersNicoletMill B24

Hydrogen 

Chloride 

(HCl) Coal 8.80E-02 184 NO

IAIAStateUnivP

owerPlant B2

Hydrogen 

Chloride 

(HCl) Coal 8.84E-02 185 NO

OHCargillDayto

n B004

Hydrogen 

Chloride 

(HCl) Coal 8.97E-02 186 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MAUMass EU#3

Hydrogen 

Chloride 

(HCl) Coal 9.23E-02 187 NO

MAUMass EU#4

Hydrogen 

Chloride 

(HCl) Coal 9.23E-02 188 NO

MAUMass EU#5

Hydrogen 

Chloride 

(HCl) Coal 9.23E-02 189 NO

OHBataviaTran

smissions Boiler 2 (B002)

Hydrogen 

Chloride 

(HCl) Coal 9.23E-02 190 NO

MOCentralElect

ricChamois UNIT 1

Hydrogen 

Chloride 

(HCl) Coal 9.40E-02 191 NO

OHAppletonIde

as Boiler 2 (B002)

Hydrogen 

Chloride 

(HCl) Coal 9.40E-02 192 NO

NCCargillFayett

eville ES-22

Hydrogen 

Chloride 

(HCl) Coal 9.43E-02 193 NO

IAIAStateUnivP

owerPlant B3

Hydrogen 

Chloride 

(HCl) Coal 9.67E-02 194 NO

MASolutiaIncSp

ringfield EU 150 S03

Hydrogen 

Chloride 

(HCl) Coal 9.68E-02 195 NO

INBungeDecatu

r B&W (1SP1)

Hydrogen 

Chloride 

(HCl) Coal 9.78E-02 196 NO

WVDuPontWas

hingtonWorks P05

Hydrogen 

Chloride 

(HCl) Coal 9.87E-02 197 NO

IAUofIowa EP6 Boiler 10

Hydrogen 

Chloride 

(HCl) Coal 9.91E-02 198 NO

WVATKRocket

Center

NB2766 W17479-W 

(Boiler 17)

Hydrogen 

Chloride 

(HCl) Coal 9.94E-02 199 NO

OHCargillAkron B001

Hydrogen 

Chloride 

(HCl) Coal 1.04E-01 200 NO

WIDomtarNeko

osa

B21 - Boiler No. 

2

Hydrogen 

Chloride 

(HCl) Coal 1.05E-01 201 NO

WIDomtarNeko

osa

B24 - Boiler No. 

10

Hydrogen 

Chloride 

(HCl) Coal 1.05E-01 202 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WIDomtarNeko

osa

B20 - Boiler No. 

1

Hydrogen 

Chloride 

(HCl) Coal 1.05E-01 203 NO

WIDomtarNeko

osa

B22 - Boiler No. 

7

Hydrogen 

Chloride 

(HCl) Coal 1.05E-01 204 NO

KYISPChemical

s 0AA (Riley)

Hydrogen 

Chloride 

(HCl) Coal 1.07E-01 205 NO

MOIP&LMissou

riCity Unit 1

Hydrogen 

Chloride 

(HCl) Coal 1.08E-01 206 NO

MOIP&LMissou

riCity Unit 2

Hydrogen 

Chloride 

(HCl) Coal 1.08E-01 207 NO

SCINVISTACa

mdenPlant

Unit ID 1 - 

Boiler No. 1

Hydrogen 

Chloride 

(HCl) Coal 1.09E-01 208 NO

SCINVISTACa

mdenPlant

Unit ID 2 - 

Boiler No. 2

Hydrogen 

Chloride 

(HCl) Coal 1.09E-01 209 NO

MIManistiquePa

per EUBLR001

Hydrogen 

Chloride 

(HCl) Coal 1.10E-01 210 NO

MIManistiquePa

per EUBLR002

Hydrogen 

Chloride 

(HCl) Coal 1.10E-01 211 NO

VARadfordArmy

AmmunitionPla

nt Boiler No. 3

Hydrogen 

Chloride 

(HCl) Coal 1.11E-01 212 NO

VARadfordArmy

AmmunitionPla

nt Boiler No. 5

Hydrogen 

Chloride 

(HCl) Coal 1.11E-01 213 NO

INBungeDecatu

r Keeler (2SP1)

Hydrogen 

Chloride 

(HCl) Coal 1.12E-01 214 NO

MOUofMissouri Boiler 7

Hydrogen 

Chloride 

(HCl) Coal 1.13E-01 215 NO

MOUofMissouri Boiler 8

Hydrogen 

Chloride 

(HCl) Coal 1.13E-01 216 NO

MOUofMissouri Boiler 9

Hydrogen 

Chloride 

(HCl) Coal 1.13E-01 217 NO

MITBSimonPow

erPlant Unit 1

Hydrogen 

Chloride 

(HCl) Coal 1.13E-01 218 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MOMallinckrodt Boiler 6

Hydrogen 

Chloride 

(HCl) Coal 1.13E-01 219 NO

TNInvistaChatta

nooga

EU002 - Boiler 

#5

Hydrogen 

Chloride 

(HCl) Coal 1.14E-01 220 NO

VADukeEnergy

Narrows Boiler #6

Hydrogen 

Chloride 

(HCl) Coal 1.14E-01 221 NO

MICityofEscana

ba EUBOILER#2

Hydrogen 

Chloride 

(HCl) Coal 1.14E-01 222 NO

WVSunocoIncN

ealPlantKenova

B602, Coal 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.15E-01 223 NO

OHAppletonIde

as Boiler 4 (B003)

Hydrogen 

Chloride 

(HCl) Coal 1.15E-01 224 NO

MIEBEddyPape

r EUBOILER5

Hydrogen 

Chloride 

(HCl) Coal 1.15E-01 225 NO

VADukeEnergy

Narrows Boiler #3

Hydrogen 

Chloride 

(HCl) Coal 1.19E-01 226 NO

VAINVISTAWa

ynesboro

2-205 (B#3) 

Boiler #3

Hydrogen 

Chloride 

(HCl) Coal 1.20E-01 227 NO

VADukeEnergy

Narrows Boiler #2

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 228 NO

IAGrainProcess

ing Boiler #1

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 229 NO

IAGrainProcess

ing Boiler #2

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 230 NO

IAGrainProcess

ing Boiler #3

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 231 NO

IAGrainProcess

ing Boiler #4

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 232 NO

IAGrainProcess

ing Boiler #6

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 233 NO

IAGrainProcess

ing Boiler #7

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 234 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILAbbottAbbott

Park Unit 4AP

Hydrogen 

Chloride 

(HCl) Coal 1.22E-01 235 NO

ILPolyOne B1

Hydrogen 

Chloride 

(HCl) Coal 1.23E-01 236 NO

MOBASFHanni

bal

Coal Fired 

Boiler #4

Hydrogen 

Chloride 

(HCl) Coal 1.23E-01 237 NO

MOBASFHanni

bal

Coal Fired 

Boiler #5

Hydrogen 

Chloride 

(HCl) Coal 1.27E-01 238 NO

TNInvistaChatta

nooga

EU002 - Boiler 

#4

Hydrogen 

Chloride 

(HCl) Coal 1.27E-01 239 NO

MINeenahPape

rMI Boiler 1

Hydrogen 

Chloride 

(HCl) Coal 1.27E-01 240 NO

TNCargillMemp

his

Stoker Boiler 

8001

Hydrogen 

Chloride 

(HCl) Coal 1.28E-01 241 NO

MIWhitePineEle

ctric Power Boiler #2

Hydrogen 

Chloride 

(HCl) Coal 1.31E-01 242 NO

VARadfordArmy

AmmunitionPla

nt Boiler No. 2

Hydrogen 

Chloride 

(HCl) Coal 1.31E-01 243 NO

VADukeEnergy

Narrows Boiler #4

Hydrogen 

Chloride 

(HCl) Coal 1.35E-01 244 NO

PABayValleyFo

odsPittsburgh Boiler No. 1

Hydrogen 

Chloride 

(HCl) Coal 1.37E-01 245 NO

PABayValleyFo

odsPittsburgh Boiler No. 2

Hydrogen 

Chloride 

(HCl) Coal 1.37E-01 246 NO

MNRochesterUt

ilities EU002

Hydrogen 

Chloride 

(HCl) Coal 1.42E-01 247 NO

INNewEnergy Riley Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.42E-01 248 NO

SCInternational

PaperEastover

No. 1 Power 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.46E-01 249 NO

INNotreDame B-3

Hydrogen 

Chloride 

(HCl) Coal 1.46E-01 250 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VADukeEnergy

Narrows Boiler #5

Hydrogen 

Chloride 

(HCl) Coal 1.48E-01 251 NO

PAPennState 31

Hydrogen 

Chloride 

(HCl) Coal 1.49E-01 252 NO

PAPennState 32

Hydrogen 

Chloride 

(HCl) Coal 1.49E-01 253 NO

PAPennState 34

Hydrogen 

Chloride 

(HCl) Coal 1.49E-01 254 NO

PAPennState 35

Hydrogen 

Chloride 

(HCl) Coal 1.49E-01 255 NO

OHOrrvilleUtiliti

es B005

Hydrogen 

Chloride 

(HCl) Coal 1.51E-01 256 NO

MIMenominee #3 Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.51E-01 257 NO

SCINVISTACa

mdenPlant

Unit ID 3 - 

Boiler No. 3

Hydrogen 

Chloride 

(HCl) Coal 1.51E-01 258 NO

SCINVISTACa

mdenPlant

Unit ID 4 - 

Boiler No. 4

Hydrogen 

Chloride 

(HCl) Coal 1.51E-01 259 NO

MIWhitePineEle

ctric Power Boiler #1

Hydrogen 

Chloride 

(HCl) Coal 1.53E-01 260 NO

WINewPageKi

mberly B21

Hydrogen 

Chloride 

(HCl) Coal 1.54E-01 261 NO

WINewPageKi

mberly B22

Hydrogen 

Chloride 

(HCl) Coal 1.54E-01 262 NO

PAARGBradfor

d 37

Hydrogen 

Chloride 

(HCl) Coal 1.55E-01 263 NO

KYMoreheadSt

ateUniv 02

Hydrogen 

Chloride 

(HCl) Coal 1.58E-01 264 NO

PABayValleyFo

odsPittsburgh Boiler No. 3

Hydrogen 

Chloride 

(HCl) Coal 1.63E-01 265 NO

PABayValleyFo

odsPittsburgh Boiler No. 4

Hydrogen 

Chloride 

(HCl) Coal 1.63E-01 266 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VADukeEnergy

Narrows Boiler #7

Hydrogen 

Chloride 

(HCl) Coal 1.63E-01 267 NO

WVBayerInstitut

e Boiler #12

Hydrogen 

Chloride 

(HCl) Coal 1.63E-01 268 NO

OHCargillSidne

y B002

Hydrogen 

Chloride 

(HCl) Coal 1.64E-01 269 NO

WVPPGMartins

ville R072-Boiler 5

Hydrogen 

Chloride 

(HCl) Coal 1.65E-01 270 NO

WVDuPontWas

hingtonWorks P03

Hydrogen 

Chloride 

(HCl) Coal 1.66E-01 271 NO

OHCargillSidne

y B001

Hydrogen 

Chloride 

(HCl) Coal 1.67E-01 272 NO

WIPCATomaha

wk B24

Hydrogen 

Chloride 

(HCl) Coal 1.68E-01 273 NO

WIPCATomaha

wk B27

Hydrogen 

Chloride 

(HCl) Coal 1.68E-01 274 NO

WIPCATomaha

wk B28

Hydrogen 

Chloride 

(HCl) Coal 1.68E-01 275 NO

ILADMQuincy EU-5003

Hydrogen 

Chloride 

(HCl) Coal 1.70E-01 276 NO

ILADMQuincy EU-5004

Hydrogen 

Chloride 

(HCl) Coal 1.70E-01 277 NO

IAUofNorthernIo

wa Boiler #4

Hydrogen 

Chloride 

(HCl) Coal 1.71E-01 278 NO

WIGreenBayPa

ckagingMillDivis

ion

Boiler B26- 

Coal Fired 

Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.72E-01 279 NO

WVPPGMartins

ville R015-Boiler 4

Hydrogen 

Chloride 

(HCl) Coal 1.73E-01 280 NO

MITBSimonPow

erPlant Unit 2

Hydrogen 

Chloride 

(HCl) Coal 1.74E-01 281 NO

MIMortonSaltM

anistee No. 6 Boiler

Hydrogen 

Chloride 

(HCl) Coal 1.78E-01 282 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCargillCharlo

tte ES-1

Hydrogen 

Chloride 

(HCl) Coal 1.84E-01 283 NO

MIPharma&Upj

ohn1178

EUEBLR43-5 

(Boiler No. 5)

Hydrogen 

Chloride 

(HCl) Coal 1.88E-01 284 NO

ILJohnDeereHa

rvester B8

Hydrogen 

Chloride 

(HCl) Coal 1.97E-01 285 NO

ILJohnDeereHa

rvester B7

Hydrogen 

Chloride 

(HCl) Coal 1.97E-01 286 NO

ILJohnDeereHa

rvester B9

Hydrogen 

Chloride 

(HCl) Coal 1.97E-01 287 NO

WVUCCSouthC

harleston B25

Hydrogen 

Chloride 

(HCl) Coal 2.01E-01 288 NO

OHRockTennCi

ncinnati B001

Hydrogen 

Chloride 

(HCl) Coal 2.14E-01 289 NO

ILADMPeoria EU-PH101

Hydrogen 

Chloride 

(HCl) Coal 2.47E-01 290 NO

ILADMPeoria EU-PH102

Hydrogen 

Chloride 

(HCl) Coal 2.47E-01 291 NO

MIPharma&Upj

ohn1178

EUEBLR43-2 

(Boiler No. 2)

Hydrogen 

Chloride 

(HCl) Coal 2.51E-01 292 NO

TNCargillMemp

his

Pulverized Coal 

Boiler (8301)

Hydrogen 

Chloride 

(HCl) Coal 3.02E-01 293 NO

MOUofMissouri Boiler 10

Hydrogen 

Chloride 

(HCl) Coal 3.65E-01 294 NO

INNotreDame B-2

Hydrogen 

Chloride 

(HCl) Coal 5.22E-01 295 NO

MICargillSalt EGBOILER5

Hydrogen 

Chloride 

(HCl) Coal 7.67E-01 296 NO

SCMichelinSan

dySprings B:02:01

Hydrogen 

Chloride 

(HCl) Gas 1 7.26E-05 1 YES

WYSinclairWyo

ming

Pt 74 #2 H2 

Plant Heater

Hydrogen 

Chloride 

(HCl) Gas 1 1.29E-04 2 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WYSinclairWyo

ming Pt 41 #9 HPB

Hydrogen 

Chloride 

(HCl) Gas 1 1.37E-04 3 NO

CTCytecWalling

ford 150 Furnace

Hydrogen 

Chloride 

(HCl) Gas 1 1.65E-04 4 NO

KSCoffeyvilleRe

finery EU-39-FH0027

Hydrogen 

Chloride 

(HCl) Gas 1 3.17E-04 5 NO

SCEastmanCol

ombia

HTM Heater #3 

(Equip ID 1101)

Hydrogen 

Chloride 

(HCl) Gas 1 3.25E-04 6 NO

NCCampLejeun

eMCB C-AS-4151-16

Hydrogen 

Chloride 

(HCl) Gas 1 5.50E-04 7 NO

LARubiconLLC

North Variants 

Boiler

Hydrogen 

Chloride 

(HCl) Gas 1 6.32E-04 8 NO

CAExxonMobilTorrance 19F-1

Hydrogen 

Chloride 

(HCl) Gas 1 2.85E-03 9 NO

MIFordWayneA

ssembly

Powerhouse 

Boiler 3

Hydrogen 

Chloride 

(HCl) Gas 1 5.16E-03 10 NO

CORockyMtnSt

eel212

Rod/Bar Mill 

Furnace 

95OPPB088

Hydrogen 

Chloride 

(HCl) Gas 1 8.59E-05 yes 1 YES

INAlcoaWarrick

Annealing 

Furnace #15

Hydrogen 

Chloride 

(HCl) Gas 1 2.46E-04 yes 2 YES

INAlcoaWarrick

Pre-Heat 

Furnace #36

Hydrogen 

Chloride 

(HCl) Gas 1 2.46E-04 yes 3 NO

ILUSSGraniteCi

ty

No. 8 

Galvanizing 

Line Furnace

Hydrogen 

Chloride 

(HCl) Gas 1 3.45E-04 yes 4 NO

UTWestinghous

e 202

Hydrogen 

Chloride 

(HCl) Gas 1 3.99E-04 yes 5 NO

INOutokumpuSt

ainlessPlate

Heppenstall 

Annealing 

Furnace

Hydrogen 

Chloride 

(HCl) Gas 1 6.51E-04 yes 6 NO

WICharterSteel P31

Hydrogen 

Chloride 

(HCl) Gas 1 1.00E-03 yes 7 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

INNucorSteel

Cold Mill 

Annealing

Hydrogen 

Chloride 

(HCl) Gas 1 1.64E-03 yes 8 NO

INArcelorMittalB

urnsHarbor

Hot Dip Coating 

Line Annealing 

Furnace

Hydrogen 

Chloride 

(HCl) Gas 1 2.70E-03 yes 9 NO

LAShellChemic

aGeismar Furnace F-S801

Hydrogen 

Chloride 

(HCl) Gas 2 1.70E-06 1 YES

INTateLyleSaga

more 21B501

Hydrogen 

Chloride 

(HCl) Gas 2 1.85E-04 2 NO

MDSeverstalSp

arrows

1BLR (No. 1 

Boiler)

Hydrogen 

Chloride 

(HCl) Gas 2 3.53E-04 3 NO

WIGPGreenBay

2818

B29 - Fluidized 

Bed Boiler #9

Hydrogen 

Chloride 

(HCl) Gas 2 3.89E-04 4 NO

INRollsRoyceIn

dianapolis 70-65

Hydrogen 

Chloride 

(HCl) Gas 2 1.15E-03 5 NO

WVMountainSt

ateCarbonFolla

nsbee S1

Hydrogen 

Chloride 

(HCl) Gas 2 1.23E-03 6 NO

SCBMWManufa

cturingCo HB03

Hydrogen 

Chloride 

(HCl) Gas 2 1.76E-03 7 NO

GAGPSRMRiin

con EU BO02

Hydrogen 

Chloride 

(HCl) Gas 2 6.53E-03 8 NO

CTElectric Boat EMU 18

Chlorine 

(Cl) Liquid 5.60E-07 1 YES

TNInvistaChatta

nooga

EU003 - 

Vaporizer #2

Hydrogen 

Chloride 

(HCl) Liquid 1.77E-04 2 YES

INUSSteelGary

Works O4B10459

Hydrogen 

Chloride 

(HCl) Liquid 2.07E-04 3 YES

VAINVISTAWa

ynesboro

2-205 (V#1) 

Vaporizer #1

Hydrogen 

Chloride 

(HCl) Liquid 2.43E-04 4 YES

NCCampLejeun

eMCB A-MP-230-40

Chlorine 

(Cl) Liquid 2.65E-04 5 YES

NCCampLejeun

eMCB A-NH-120-04

Chlorine 

(Cl) Liquid 2.65E-04 6 YES

NCCampLejeun

eMCB A-NH-118-03

Chlorine 

(Cl) Liquid 2.65E-04 7 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeun

eMCB A-NH-100-05

Chlorine 

(Cl) Liquid 2.65E-04 8 YES

NCCampLejeun

eMCB A-NH-100-02

Chlorine 

(Cl) Liquid 2.65E-04 9 YES

NCCampLejeun

eMCB A-NH-100-01

Chlorine 

(Cl) Liquid 2.65E-04 10 YES

NCCampLejeun

eMCB A-MP-625-74

Chlorine 

(Cl) Liquid 2.65E-04 11 YES

NCCampLejeun

eMCB A-NH-120-H4

Chlorine 

(Cl) Liquid 2.65E-04 12 YES

NCCampLejeun

eMCB A-MP-625-72

Chlorine 

(Cl) Liquid 2.65E-04 13 YES

NCCampLejeun

eMCB A-PP-1943-08

Chlorine 

(Cl) Liquid 2.65E-04 14 YES

NCCampLejeun

eMCB A-MP-230-39

Chlorine 

(Cl) Liquid 2.65E-04 15 YES

NCCampLejeun

eMCB A-MP-230-38

Chlorine 

(Cl) Liquid 2.65E-04 16 YES

NCCampLejeun

eMCB A-MG-SH8-58

Chlorine 

(Cl) Liquid 2.65E-04 17 YES

NCCampLejeun

eMCB A-MP-625-73

Chlorine 

(Cl) Liquid 2.65E-04 18 YES

NCCampLejeun

eMCB A-LCH-4022-19

Chlorine 

(Cl) Liquid 2.65E-04 19 YES

NCCampLejeun

eMCB A-NH-121-H1

Chlorine 

(Cl) Liquid 2.65E-04 20 YES

NCCampLejeun

eMCB A-HP-738-59

Chlorine 

(Cl) Liquid 2.65E-04 21 YES

NCCampLejeun

eMCB A-PP-1943-H7

Chlorine 

(Cl) Liquid 2.65E-04 22 YES

NCCampLejeun

eMCB A-PP-2615-09

Chlorine 

(Cl) Liquid 2.65E-04 23 YES

NCCampLejeun

eMCB A-PP-2615-10

Chlorine 

(Cl) Liquid 2.65E-04 24 NO

NCCampLejeun

eMCB A-TT-2457-66

Chlorine 

(Cl) Liquid 2.65E-04 25 NO

NCCampLejeun

eMCB A-TT-44-30

Chlorine 

(Cl) Liquid 2.65E-04 26 NO

NCCampLejeun

eMCB A-TT-60-78

Chlorine 

(Cl) Liquid 2.65E-04 27 NO

NCCampLejeun

eMCB B-A66-48

Chlorine 

(Cl) Liquid 2.65E-04 28 NO

NCCampLejeun

eMCB B-A71-49

Chlorine 

(Cl) Liquid 2.65E-04 29 NO

NCCampLejeun

eMCB B-A71-H5

Chlorine 

(Cl) Liquid 2.65E-04 30 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeun

eMCB B-A-A1-50

Chlorine 

(Cl) Liquid 2.65E-04 31 NO

NCCampLejeun

eMCB A-NH-121-01

Chlorine 

(Cl) Liquid 2.65E-04 32 NO

NCCampLejeun

eMCB A-FC-989-31

Chlorine 

(Cl) Liquid 2.65E-04 33 NO

NCCampLejeun

eMCB C-CG-650-83B

Chlorine 

(Cl) Liquid 2.65E-04 34 NO

NCCampLejeun

eMCB A-BM-5400-80

Chlorine 

(Cl) Liquid 2.65E-04 35 NO

NCCampLejeun

eMCB A-BM-5400-81

Chlorine 

(Cl) Liquid 2.65E-04 36 NO

NCCampLejeun

eMCB A-BM-825-12

Chlorine 

(Cl) Liquid 2.65E-04 37 NO

NCCampLejeun

eMCB A-BM-825-13

Chlorine 

(Cl) Liquid 2.65E-04 38 NO

NCCampLejeun

eMCB A-BM-825-H1

Chlorine 

(Cl) Liquid 2.65E-04 39 NO

NCCampLejeun

eMCB A-BM-835-06

Chlorine 

(Cl) Liquid 2.65E-04 40 NO

NCCampLejeun

eMCB A-BM-835-07

Chlorine 

(Cl) Liquid 2.65E-04 41 NO

NCCampLejeun

eMCB A-BM-890-14

Chlorine 

(Cl) Liquid 2.65E-04 42 NO

NCCampLejeun

eMCB A-BM-890-15

Chlorine 

(Cl) Liquid 2.65E-04 43 NO

NCCampLejeun

eMCB A-BM-890-H10

Chlorine 

(Cl) Liquid 2.65E-04 44 NO

NCCampLejeun

eMCB A-BM-890-H9

Chlorine 

(Cl) Liquid 2.65E-04 45 NO

NCCampLejeun

eMCB A-LCH-4014-17

Chlorine 

(Cl) Liquid 2.65E-04 46 NO

NCCampLejeun

eMCB A-FC-440-87

Chlorine 

(Cl) Liquid 2.65E-04 47 NO

NCCampLejeun

eMCB B-A-A47-51

Chlorine 

(Cl) Liquid 2.65E-04 48 NO

NCCampLejeun

eMCB A-HP-1700-05

Chlorine 

(Cl) Liquid 2.65E-04 49 NO

NCCampLejeun

eMCB A-HP-2027-20

Chlorine 

(Cl) Liquid 2.65E-04 50 NO

NCCampLejeun

eMCB A-HP-2027-21

Chlorine 

(Cl) Liquid 2.65E-04 51 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeun

eMCB A-HP-2027-H13

Chlorine 

(Cl) Liquid 2.65E-04 52 NO

NCCampLejeun

eMCB A-HP-2027-H14

Chlorine 

(Cl) Liquid 2.65E-04 53 NO

NCCampLejeun

eMCB A-HP-2027-H15

Chlorine 

(Cl) Liquid 2.65E-04 54 NO

NCCampLejeun

eMCB A-HP-2027-H16

Chlorine 

(Cl) Liquid 2.65E-04 55 NO

NCCampLejeun

eMCB A-HP-40-75

Chlorine 

(Cl) Liquid 2.65E-04 56 NO

NCCampLejeun

eMCB A-HP-40-76

Chlorine 

(Cl) Liquid 2.65E-04 57 NO

NCCampLejeun

eMCB A-HP-500-86

Chlorine 

(Cl) Liquid 2.65E-04 58 NO

NCCampLejeun

eMCB A-HP-670-88

Chlorine 

(Cl) Liquid 2.65E-04 59 NO

NCCampLejeun

eMCB B-A66-H3

Chlorine 

(Cl) Liquid 2.65E-04 60 NO

NCCampLejeun

eMCB A-HP-989-31

Chlorine 

(Cl) Liquid 2.65E-04 61 NO

NCCampLejeun

eMCB A-FC-260-90

Chlorine 

(Cl) Liquid 2.65E-04 62 NO

NCCampLejeun

eMCB C-AS-843-14

Chlorine 

(Cl) Liquid 2.65E-04 63 NO

NCCampLejeun

eMCB B-BB-49-52

Chlorine 

(Cl) Liquid 2.65E-04 64 NO

NCCampLejeun

eMCB C-AS-1000-H21

Chlorine 

(Cl) Liquid 2.65E-04 65 NO

NCCampLejeun

eMCB A-TT-60-79

Chlorine 

(Cl) Liquid 2.65E-04 66 NO

NCCampLejeun

eMCB C-AS-3502-08

Chlorine 

(Cl) Liquid 2.65E-04 67 NO

NCCampLejeun

eMCB C-AS-3504-09

Chlorine 

(Cl) Liquid 2.65E-04 68 NO

NCCampLejeun

eMCB C-AS-3525-15

Chlorine 

(Cl) Liquid 2.65E-04 69 NO

NCCampLejeun

eMCB C-AS-4044-22

Chlorine 

(Cl) Liquid 2.65E-04 70 NO

NCCampLejeun

eMCB C-AS-4044-23

Chlorine 

(Cl) Liquid 2.65E-04 71 NO

NCCampLejeun

eMCB C-AS-4151-17A

Chlorine 

(Cl) Liquid 2.65E-04 72 NO

NCCampLejeun

eMCB C-AS-4151-18

Chlorine 

(Cl) Liquid 2.65E-04 73 NO

NCCampLejeun

eMCB C-AS-705-11

Chlorine 

(Cl) Liquid 2.65E-04 74 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeun

eMCB B-BB-9-55

Chlorine 

(Cl) Liquid 2.65E-04 75 NO

NCCampLejeun

eMCB C-AS-840-13

Chlorine 

(Cl) Liquid 2.65E-04 76 NO

NCCampLejeun

eMCB C-AS-1000-20

Chlorine 

(Cl) Liquid 2.65E-04 77 NO

NCCampLejeun

eMCB C-CG-480-89

Chlorine 

(Cl) Liquid 2.65E-04 78 NO

NCCampLejeun

eMCB

C-VL-TFM204-

02

Chlorine 

(Cl) Liquid 2.65E-04 79 NO

NCCampLejeun

eMCB

C-VL-TFM204-

01

Chlorine 

(Cl) Liquid 2.65E-04 80 NO

NCCampLejeun

eMCB

C-VL-TFM203-

02

Chlorine 

(Cl) Liquid 2.65E-04 81 NO

NCCampLejeun

eMCB

C-VL-TFM203-

01

Chlorine 

(Cl) Liquid 2.65E-04 82 NO

NCCampLejeun

eMCB

C-VL-TFM104-

01

Chlorine 

(Cl) Liquid 2.65E-04 83 NO

NCCampLejeun

eMCB

C-VL-TFM103-

01

Chlorine 

(Cl) Liquid 2.65E-04 84 NO

NCCampLejeun

eMCB C-TC-1500-60

Chlorine 

(Cl) Liquid 2.65E-04 85 NO

NCCampLejeun

eMCB C-RR-15-46B

Chlorine 

(Cl) Liquid 2.65E-04 86 NO

NCCampLejeun

eMCB C-CG-650-85

Chlorine 

(Cl) Liquid 2.65E-04 87 NO

NCCampLejeun

eMCB C-CG-650-84B

Chlorine 

(Cl) Liquid 2.65E-04 88 NO

NCCampLejeun

eMCB C-AS-710-03

Chlorine 

(Cl) Liquid 2.65E-04 89 NO

NCCampLejeun

eMCB C-AS-2800-12

Chlorine 

(Cl) Liquid 2.65E-04 90 NO

NCCampLejeun

eMCB B-BB-9-53B

Chlorine 

(Cl) Liquid 2.65E-04 91 NO

NCCampLejeun

eMCB B-BB-9-54

Chlorine 

(Cl) Liquid 2.65E-04 92 NO

PABoeingRidley

Park 033

Hydrogen 

Chloride 

(HCl) Liquid 4.21E-04 93 NO

CTElectric Boat EMU 17

Hydrogen 

Chloride 

(HCl) Liquid 4.21E-04 94 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

SCDAKAmerica

s P8F

Hydrogen 

Chloride 

(HCl) Liquid 4.23E-04 95 NO

MEFPLEnergy

Wyman Unit #5

Hydrogen 

Chloride 

(HCl) Liquid 4.89E-04 96 NO

NCMCASCherr

yPoint

CP-152-BOIL03

Hydrogen 

Chloride 

(HCl) Liquid 7.00E-04 97 NO

MNGPDuluth EU33 Boiler #3

Hydrogen 

Chloride 

(HCl) Liquid 7.42E-04 98 NO

MIConsumerEn

ergyCoCampbell EUAUXBLR12

Hydrogen 

Chloride 

(HCl) Liquid 7.78E-04 99 NO

NJVinelandMun

iElectricHowardDown Unit 9

Hydrogen 

Chloride 

(HCl) Liquid 8.22E-04 100 NO

NCInvistaHwy4

21 B7600

Hydrogen 

Chloride 

(HCl) Liquid 8.25E-04 101 NO

MNMinnesotaS

oybeanProcess

ors Boiler 1 EU026

Hydrogen 

Chloride 

(HCl) Liquid 8.73E-04 102 NO

MNMinnesotaS

oybeanProcess

ors Boiler 2 EU027

Hydrogen 

Chloride 

(HCl) Liquid 8.73E-04 103 NO

SCINVISTACa

mdenPlant

Unit ID 8 - 

Vaporizer No. 3

Hydrogen 

Chloride 

(HCl) Liquid 1.00E-03 104 NO

SCINVISTACa

mdenPlant

Unit ID 9 - 

Vaporizer No. 4

Hydrogen 

Chloride 

(HCl) Liquid 1.00E-03 105 NO

VANewportNew

sShipbuildingDr

yDock 78-E1

Hydrogen 

Chloride 

(HCl) Liquid 1.14E-03 106 NO

TNMilanArmyA

mmunitionPlant

I5A-1, Source 

#27-0010-14

Chlorine 

(Cl) Liquid 1.51E-03 107 NO

TNMilanArmyA

mmunitionPlant

I4A-1, Source 

#27-0010-13

Chlorine 

(Cl) Liquid 1.51E-03 108 NO

TNMilanArmyA

mmunitionPlant

I3A-1, Source 

#27-0010-12

Chlorine 

(Cl) Liquid 1.51E-03 109 NO

TNMilanArmyA

mmunitionPlant

F52L-2, Source 

#27-0010-30

Chlorine 

(Cl) Liquid 1.51E-03 110 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TNMilanArmyA

mmunitionPlant

T116A-2, 

Source #27-

0010-84

Chlorine 

(Cl) Liquid 1.51E-03 111 NO

TNMilanArmyA

mmunitionPlant

I6A-1, Source 

#27-0010-15

Chlorine 

(Cl) Liquid 1.51E-03 112 NO

TNMilanArmyA

mmunitionPlant

D2A-1, Source 

#27-0010-09

Chlorine 

(Cl) Liquid 1.51E-03 113 NO

TNMilanArmyA

mmunitionPlant

F52L-1, Source 

#27-0010-30

Chlorine 

(Cl) Liquid 1.51E-03 114 NO

TNMilanArmyA

mmunitionPlant

B21L-2, Source 

#27-0010-28

Chlorine 

(Cl) Liquid 1.51E-03 115 NO

TNMilanArmyA

mmunitionPlant

B21L-1, Source 

#27-0010-28

Chlorine 

(Cl) Liquid 1.51E-03 116 NO

TNMilanArmyA

mmunitionPlant

A15L-2, Source 

#27-0010-05

Chlorine 

(Cl) Liquid 1.51E-03 117 NO

TNMilanArmyA

mmunitionPlant

A15L-1, Source 

#27-0010-05

Chlorine 

(Cl) Liquid 1.51E-03 118 NO

TNMilanArmyA

mmunitionPlant

D88L-2, Source 

#27-0010-86

Chlorine 

(Cl) Liquid 1.51E-03 119 NO

TNMilanArmyA

mmunitionPlant

X21L-2, Source 

#27-0010-29

Chlorine 

(Cl) Liquid 1.51E-03 120 NO

TNMilanArmyA

mmunitionPlant

V1L-1, Source 

#27-0010-46

Chlorine 

(Cl) Liquid 1.51E-03 121 NO

TNMilanArmyA

mmunitionPlant

D88L-1, Source 

#27-0010-86

Chlorine 

(Cl) Liquid 1.51E-03 122 NO

TNMilanArmyA

mmunitionPlant

X21L-1, Source 

#27-0010-29

Chlorine 

(Cl) Liquid 1.51E-03 123 NO

TNMilanArmyA

mmunitionPlant

I7A-1, Source 

#27-0010-16

Chlorine 

(Cl) Liquid 1.51E-03 124 NO

TNMilanArmyA

mmunitionPlant

X21L-3, Source 

#27-0010-29

Chlorine 

(Cl) Liquid 1.51E-03 125 NO

TNMilanArmyA

mmunitionPlant

T116A-1, 

Source #27-

0010-84

Chlorine 

(Cl) Liquid 1.51E-03 126 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TNMilanArmyA

mmunitionPlant

S101A-2, 

Source #27-

0010-21

Chlorine 

(Cl) Liquid 1.51E-03 127 NO

TNMilanArmyA

mmunitionPlant

J107A-1, 

Source #27-

0010-31

Chlorine 

(Cl) Liquid 1.51E-03 128 NO

TNMilanArmyA

mmunitionPlant

K313A-2, 

Source #27-

0010-83

Chlorine 

(Cl) Liquid 1.51E-03 129 NO

TNMilanArmyA

mmunitionPlant

K313A-1, 

Source #27-

0010-83

Chlorine 

(Cl) Liquid 1.51E-03 130 NO

TNMilanArmyA

mmunitionPlant

K300A-2, 

Source #27-

0010-19

Chlorine 

(Cl) Liquid 1.51E-03 131 NO

TNMilanArmyA

mmunitionPlant

K300A-1, 

Source #27-

0010-19

Chlorine 

(Cl) Liquid 1.51E-03 132 NO

TNMilanArmyA

mmunitionPlant

K102L-1, 

Source #27-

0010-42

Chlorine 

(Cl) Liquid 1.51E-03 133 NO

TNMilanArmyA

mmunitionPlant

J107A-2, 

Source #27-

0010-31

Chlorine 

(Cl) Liquid 1.51E-03 134 NO

TNMilanArmyA

mmunitionPlant

S101A-1, 

Source #27-

0010-21

Chlorine 

(Cl) Liquid 1.51E-03 135 NO

SCGPChemRu

ssellville FO Boiler

Hydrogen 

Chloride 

(HCl) Liquid 1.67E-03 136 NO

VASmurfitStone

Westpt PB08

Hydrogen 

Chloride 

(HCl) Liquid 1.82E-03 137 NO

NCMCASCherr

yPoint

CP-1786-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 138 NO

NCMCASCherr

yPoint

CP-1783-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 139 NO

NCMCASCherr

yPoint

CP-1782-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 140 NO

NCMCASCherr

yPoint

CP-1781-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 141 NO

NCMCASCherr

yPoint

CP-1780-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 142 NO

NCMCASCherr

yPoint

CP-1779-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 143 NO

NCMCASCherr

yPoint

CP-1777-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 144 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCMCASCherr

yPoint

CP-4344-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 145 NO

NCMCASCherr

yPoint

CP-1229-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 146 NO

NCMCASCherr

yPoint

CP-1787-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 147 NO

NCMCASCherr

yPoint

CP-152-BOIL04Chlorine 

(Cl) Liquid 2.05E-03 148 NO

NCMCASCherr

yPoint

CP-4639-BOIL02Chlorine 

(Cl) Liquid 2.05E-03 149 NO

NCMCASCherr

yPoint

CP-4402-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 150 NO

NCMCASCherr

yPoint

CP-4465-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 151 NO

NCMCASCherr

yPoint

CP-4563-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 152 NO

NCMCASCherr

yPoint

CP-4564-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 153 NO

NCMCASCherr

yPoint

CP-4571-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 154 NO

NCMCASCherr

yPoint

CP-4571-BOIL02Chlorine 

(Cl) Liquid 2.05E-03 155 NO

NCMCASCherr

yPoint

CP-4401-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 156 NO

NCMCASCherr

yPoint

CP-4639-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 157 NO

NCMCASCherr

yPoint

CP-487-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 158 NO

NCMCASCherr

yPoint

CP-4639-BOIL03Chlorine 

(Cl) Liquid 2.05E-03 159 NO

NCMCASCherr

yPoint

CP-4810-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 160 NO

NCMCASCherr

yPoint

CP-486-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 161 NO

NCMCASCherr

yPoint

CP-486-BOIL02Chlorine 

(Cl) Liquid 2.05E-03 162 NO

NCMCASCherr

yPoint

CP-487-BOIL02Chlorine 

(Cl) Liquid 2.05E-03 163 NO

NCMCASCherr

yPoint

CP-1791-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 164 NO

NCMCASCherr

yPoint

CP-4213-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 165 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCMCASCherr

yPoint

CP-4576-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 166 NO

NCMCASCherr

yPoint

CP-3916-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 167 NO

NCMCASCherr

yPoint

CP-1799-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 168 NO

NCMCASCherr

yPoint

CP-1795-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 169 NO

NCMCASCherr

yPoint

CP-192-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 170 NO

NCMCASCherr

yPoint

CP-248-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 171 NO

NCMCASCherr

yPoint

CP-3919-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 172 NO

NCMCASCherr

yPoint

CP-4041-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 173 NO

NCMCASCherr

yPoint

CP-4049-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 174 NO

NCMCASCherr

yPoint

CP-4298-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 175 NO

NCMCASCherr

yPoint

CP-4390-BOIL02Chlorine 

(Cl) Liquid 2.05E-03 176 NO

NCMCASCherr

yPoint

CP-4390-BOIL03Chlorine 

(Cl) Liquid 2.05E-03 177 NO

NCMCASCherr

yPoint

CP-4390-BOIL01Chlorine 

(Cl) Liquid 2.05E-03 178 NO

NCCampLejeun

eMCB C-RR-15-47B

Hydrogen 

Chloride 

(HCl) Liquid 2.07E-03 179 NO

MINeenahPape

rMI Boiler 2

Chlorine 

(Cl) Liquid 3.19E-03 180 NO

ALGPBrewtonM

ill

BR-PSG0-S018 

No. 1 Power 

Boiler

Chlorine 

(Cl) Liquid 3.20E-03 181 NO

NYConEd59thS

tStationNewYor

k Boiler 118

Hydrogen 

Chloride 

(HCl) Liquid 3.67E-03 182 NO

NCCampLejeun

eMCB C-AS-4151-16

Hydrogen 

Chloride 

(HCl) Liquid 7.33E-03 183 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 2-HCl Floor

FacilityID

CombustorID_c

ommon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCDomtar

66-25-2050 

(No. 1 Package 

Boiler)

Hydrogen 

Chloride 

(HCl) Liquid 7.90E-03 184 NO

MESDWarrenS

omerset Package Boiler

Chlorine 

(Cl) Liquid 8.72E-03 185 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

GAGPCelluloseB

runswick

U700 -- No. 4 

Power Boiler Particulate Biomass 5.33E-04 1 YES

MNAndersonCor

pBayport Boiler 11 EU620 Particulate Biomass 6.00E-04 2 YES

MNAndersonCor

pBayport Boiler 12 EU621 Particulate Biomass 6.00E-04 3 YES

WAWeyerhaeuse

r_Raymond

Hog Fuel Boiler 

EU1 Particulate Biomass 6.33E-04 4 YES

ARPotlatchForest

Warren Wellons Boiler Particulate Biomass 8.00E-04 5 YES

ARWeyerhaeuser

DierksMill SN-45 Particulate Biomass 1.37E-03 6 YES

ARWeyerhaeuser

DierksMill SN-32 Particulate Biomass 1.73E-03 7 YES

MSGPNewAugus

ta

AA-015 Power 

Boiler Particulate Biomass 1.80E-03 8 YES

IDRileyCreekLum

ber HFB1 Particulate Biomass 2.11E-03 9 YES

FLUSSugarCorp Boiler No. 8 Particulate Biomass 2.23E-03 10 YES

FLSmurfit-Stone 5PB Particulate Biomass 2.67E-03 11 YES

WIDomtar2814 B11, S11 Particulate Biomass 3.10E-03 12 YES

MSWeyerhaeuse

rBruce

AA-002 No. 2 

Boiler Particulate Biomass 3.33E-03 13 YES

LAWeyerhaeuser

Dodson ES-017 WFB Particulate Biomass 3.33E-03 14 NO

ARLeolaLumber

Mill SN-01A Particulate Biomass 3.67E-03 15 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

SCNewSouthCo

Conway WWB1 Particulate Biomass 5.10E-03 16 NO

FLUSSugarCorp Boiler No. 7 Particulate Biomass 5.33E-03 17 NO

ARLeolaLumber

Mill SN-01B Particulate Biomass 5.57E-03 18 NO

OKWeyerhaeuse

rWrightCity EUG 19 Particulate Biomass 5.80E-03 19 NO

ORBBSMMedfor

d B1 Particulate Biomass 6.33E-03 20 NO

ORBBSMMedfor

d B3 Particulate Biomass 6.33E-03 21 NO

ORBBSMMedfor

d B2 Particulate Biomass 6.33E-03 22 NO

MNDESPHansO

Nyman EU007 Particulate Biomass 6.67E-03 23 NO

SCNewSouthCa

mden WWB1 Particulate Biomass 7.10E-03 24 NO

SCSmurfitStone Unit 15: Boiler #3 Particulate Biomass 9.17E-03 25 NO

ALManningtonW

oodFloors BB01 Particulate Biomass 9.67E-03 26 NO

ALManningtonW

oodFloors BB02 Particulate Biomass 9.67E-03 27 NO

GARayonierBaxle

y PB02 Particulate Biomass 1.18E-02 28 NO

MNHibbing Unit 4A Particulate Biomass 1.20E-02 29 NO

CARoseburgWee

d Boiler Particulate Biomass 1.65E-02 30 NO

ORBlueHeronPa

per G Boiler Particulate Biomass 1.80E-02 31 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WABoiseKettleFa

llsPlywood B1 Particulate Biomass 1.80E-02 32 NO

ARGBPMorrilton SN-04 Particulate Biomass 1.99E-02 33 NO

IDChilcoLakeSaw

mill HFB1 Particulate Biomass 2.09E-02 34 NO

ARPotlatchForest

Prescott McBurney Boiler Particulate Biomass 2.36E-02 35 NO

ALGPBelkLumbe

r

EU 001 Wood 

Fired Boiler Particulate Biomass 2.67E-02 36 NO

IDMoyieSprings 

Lumber420 HFB1 Particulate Biomass 2.90E-02 37 NO

GAInternationalP

aperAugustaMills PB3A Particulate Biomass 3.17E-02 38 NO

GAGPWarrenton

400B Wood 

Waste Boiler Particulate Biomass 3.53E-02 39 NO

GAGPWoodClaxt

on 400 Particulate Biomass 3.67E-02 40 NO

TXNorbordTexas

Nacogdoches Konus No. 1 Particulate Biomass 3.73E-02 41 NO

TXNorbordTexas

Nacogdoches Konus No. 2 Particulate Biomass 3.73E-02 42 NO

LABoiseCascade

Oakdale B-1 Particulate Biomass 3.87E-02 43 NO

MNHill Boiler 2 Particulate Biomass 4.37E-02 44 NO

GAWeyerhaeuse

rCoOglethorpe

Power Boiler 

(U400) Particulate Biomass 4.47E-02 45 NO

IDRileyCreekLum

ber HFB2 Particulate Biomass 4.50E-02 46 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXwestfraser Boiler-1 Particulate Biomass 4.52E-02 47 NO

NCSeaboardLum

ber ES-3 Particulate Biomass 5.24E-02 48 NO

FLSugarCaneGro

wersCoop Boiler No. 3 Particulate Biomass 5.60E-02 49 NO

GAGPWarmSprin

gs

EU600 Wood 

Fuel Boiler Particulate Biomass 6.10E-02 50 NO

OKPanPacificPro

ducts EU 100 Particulate Biomass 6.11E-02 51 NO

GAPCAValdosta 1005 Particulate Biomass 6.23E-02 52 NO

GAPCAValdosta 1006 Particulate Biomass 6.23E-02 53 NO

FLSugarCaneGro

wersCoop Boiler No. 5 Particulate Biomass 6.27E-02 54 NO

FLSugarCaneGro

wersCoop Boiler No. 8 Particulate Biomass 6.27E-02 55 NO

MNHill Boiler 1 Particulate Biomass 6.47E-02 56 NO

NYIntlPaperTicon

deroga PB1 Particulate Biomass 6.77E-02 57 NO

FLUSSugarCorp Boiler No. 4 Particulate Biomass 6.97E-02 58 NO

ALWestFraserMa

plesville Boiler-1 Particulate Biomass 7.04E-02 59 NO

FLSugarCaneGro

wersCoop Boiler No. 4 Particulate Biomass 7.23E-02 60 NO

HIPuuneneSugar

Mill Boiler 1 Particulate Biomass 8.11E-02 61 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

HIPuuneneSugar

Mill Boiler 2 Particulate Biomass 8.11E-02 62 NO

FLSugarCaneGro

wersCoop Boiler No. 2 Particulate Biomass 9.00E-02 63 NO

NDCargillWestFa

rgo

Foster Wheeler 

Boiler (EU43) Particulate Biomass 9.03E-02 64 NO

GARayonierJesu

pMill PB02 Particulate Biomass 9.33E-02 65 NO

FLOsceolaFarms Boiler No. 6 Particulate Biomass 9.37E-02 66 NO

GARayonierJesu

pMill PB03 Particulate Biomass 9.90E-02 67 NO

FLOsceolaFarms Boiler No. 3 Particulate Biomass 1.06E-01 68 NO

FLUSSugarCorp Boiler No. 1 Particulate Biomass 1.07E-01 69 NO

WAGraysHarbor

Paper

No. 8 Boiler 

(EU1) Particulate Biomass 1.10E-01 70 NO

MNNorbordMinne

sota Konus No. 1 Particulate Biomass 1.14E-01 71 NO

ALIPPineHill 109-0001-Z007 Particulate Biomass 1.14E-01 72 NO

MNNorbordMinne

sota Konus No. 2 Particulate Biomass 1.14E-01 73 NO

TXAnthonyForest

Prod-ATL EP 10.1 Superior Particulate Biomass 1.14E-01 74 NO

GARayonierJesu

pMill PB01 Particulate Biomass 1.14E-01 75 NO

GARayonierBaxle

y PB01 Particulate Biomass 1.17E-01 76 NO

ORRosboroSprin

gfield DV 01.1 Particulate Biomass 1.20E-01 77 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

FLUSSugarCorp Boiler No. 2 Particulate Biomass 1.27E-01 78 NO

ARAnthonyForest

Products SN-12 Particulate Biomass 1.29E-01 79 NO

FLGPPalatka EU16 Particulate Biomass 1.30E-01 80 NO

NCGPDudley ES-B1 Particulate Biomass 1.33E-01 81 NO

TXAnthonyForest

Prod-ATL EP 11.1 Hurst Particulate Biomass 1.42E-01 82 NO

FLOsceolaFarms Boiler No. 5 Particulate Biomass 1.45E-01 83 NO

FLOsceolaFarms Boiler No. 4 Particulate Biomass 1.49E-01 84 NO

MEDomtarBailey

ville #9 Power Boiler Particulate Biomass 1.50E-01 85 NO

FLOsceolaFarms Boiler No. 2 Particulate Biomass 1.53E-01 86 NO

ARWestFraserHu

ttig SN-24 Particulate Biomass 1.83E-01 87 NO

WAGraysHarbor

Paper

No. 6 Boiler 

(EU2) Particulate Biomass 2.04E-01 88 NO

MIWhitePineElec

tric IBW Boiler Particulate Biomass 2.13E-01 89 NO

SCNewSouthLum

berCoDarlington BLR1 Particulate Biomass 2.16E-01 90 NO

ORWeyerhaeuse

rCoWarrentonLu

mberMill 3-HFB Particulate Biomass 2.23E-01 91 NO

LABoiseCascade

Florien B-1 Particulate Biomass 2.31E-01 92 NO

SCCollumsLumb

er 01 Particulate Biomass 2.33E-01 93 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ARWestFraserHu

ttig SN-01 Particulate Biomass 2.44E-01 94 NO

SCNewSouthLum

berCoDarlington BLR3 Particulate Biomass 2.54E-01 95 NO

ARGBPMorrilton SN-02 Particulate Biomass 2.60E-01 96 NO

MSWeyerhaeuse

rBruce

AA-001 No. 1 

Boiler Particulate Biomass 2.69E-01 97 NO

NCGPRoxboro

ES-1 Wood fired 

Boiler Particulate Biomass 2.84E-01 98 NO

MILPCSagola TOH-Wood Particulate Biomass 2.90E-01 99 NO

ARWeyerhaeuser SN-06 Particulate Biomass 2.98E-01 100 NO

ALWeyerhaeuser

Millport Boiler No. 1 Particulate Biomass 3.15E-01 101 NO

ARDeltaNaturalKr

aft

Hog Fuel Boiler 

(SN-05) Particulate Biomass 3.32E-01 102 NO

ALBrewton SB-1 Particulate Biomass 3.33E-01 103 NO

SCSmurfitStone Unit 15: Boiler #1 Particulate Biomass 3.39E-01 104 NO

MSBatesvilleMfg AA-001 Particulate Biomass 3.46E-01 105 NO

MSBatesvilleMfg AA-002 Particulate Biomass 4.68E-01 106 NO

MSWeyerhaeuse

r1398 Boiler No. 1 Particulate Biomass 5.09E-01 107 NO

MSWeyerhaeuse

r1398 Boiler No. 2 Particulate Biomass 2.23E+00 108 NO

IAArchersDaniels

MidlandDesMoin

es Asea Boiler #1 Particulate Coal 2.00E-04 1 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IAUofNorthernIow

a Boiler #3 Particulate Coal 5.91E-04 2 YES

VAUniversityofVir

ginia 7103-1-01R Particulate Coal 6.00E-04 3 YES

IAIAStateUnivPo

werPlant B2 Particulate Coal 6.08E-04 4 YES

WIGreenBayPac

kagingMillDivision

Boiler B26- Coal 

Fired Boiler Particulate Coal 6.40E-04 5 YES

TNCargillMemphi

s

Stoker Boiler 

8001 Particulate Coal 7.12E-04 6 YES

TNEastman_NO_

CBIDATA Boiler 25 Particulate Coal 8.67E-04 7 YES

IAIAStateUnivPo

werPlant B1 Particulate Coal 1.00E-03 8 YES

OHSmartPapers

HoldingsLLC B010 Particulate Coal 1.00E-03 9 YES

TNEastman_NO_

CBIDATA Boiler 27 Particulate Coal 1.20E-03 10 YES

WINewPageBiron B24 Particulate Coal 1.37E-03 11 YES

IDTASCONampa Riley Boiler Particulate Coal 1.44E-03 12 YES

INSABICInnovati

vePlastics

01-001 BW1 

Boiler Particulate Coal 1.53E-03 13 YES

INSABICInnovati

vePlastics

01-001 BW2 

Boiler Particulate Coal 1.53E-03 14 YES

MNAmericanCrys

talCrookston Boiler 1 Particulate Coal 1.73E-03 15 YES

IAADMCornProce

ssingCR EU-502B Particulate Coal 2.20E-03 16 YES

WIWausau

# 5 Power Boiler 

(B24) Particulate Coal 2.31E-03 17 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

AKDoyonUtilities

_AK 4 Particulate Coal 2.33E-03 18 YES

INPurdueUniveris

ity Boiler 5 Particulate Coal 2.33E-03 19 YES

VAUniversityofVir

ginia 7103-1-02R Particulate Coal 2.33E-03 20 YES

TNEastman_NO_

CBIDATA Boiler 30 Particulate Coal 2.60E-03 21 YES

ILRockIslandArse

nal

NBN 12602 

(Boiler #1) Particulate Coal 2.69E-03 22 YES

OHUofCincinnati B108 Particulate Coal 2.78E-03 23 YES

SCInternationalP

aperEastover

No. 1 Power 

Boiler Particulate Coal 2.90E-03 24 YES

WIThilmanyPape

rsNicoletMill B23 Particulate Coal 2.94E-03 25 YES

WIThilmanyPape

rsNicoletMill B24 Particulate Coal 2.94E-03 26 YES

IDAmalgamatedS

ugarCoTwinFalls S-B1 Particulate Coal 3.13E-03 27 YES

ILPolyOne B1 Particulate Coal 3.20E-03 28 YES

TNEastman_NO_

CBIDATA Boiler 31 Particulate Coal 3.47E-03 29 YES

IAUofIowa EP7 Boiler 11 Particulate Coal 3.53E-03 30 YES

ILAbbottAbbottPa

rk Unit 5AP Particulate Coal 3.59E-03 31 YES

VADukeEnergyN

arrows Boiler #2 Particulate Coal 3.67E-03 32 YES

OHSmartPapers

HoldingsLLC B020 Particulate Coal 3.73E-03 33 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

AKDoyonUtilities

_AK 7 Particulate Coal 3.83E-03 34 YES

VAGPBigIsland2

703

PWR04 - No. 4 

Power Boiler Particulate Coal 4.00E-03 35 YES

VAUniversityofVir

ginia 7103-1-05 Particulate Coal 4.20E-03 36 YES

VADukeEnergyN

arrows Boiler #3 Particulate Coal 4.33E-03 37 YES

INNotreDame B-4 Particulate Coal 4.50E-03 38 YES

NCHanesDyeWin

stonSalem ES B01 Particulate Coal 4.63E-03 39 YES

NCHanesDyeWin

stonSalem ES B02 Particulate Coal 4.63E-03 40 YES

OKGPMuskogee

Mill B-3 Particulate Coal 4.67E-03 41 YES

TNEastman_NO_

CBIDATA Boiler 26 Particulate Coal 4.67E-03 42 NO

TNEastman_NO_

CBIDATA Boiler 28 Particulate Coal 4.70E-03 43 NO

IARoquetteAmeri

ca

Circulating 

Fluidized Bed 

Boiler (121) Particulate Coal 4.74E-03 44 NO

MIHollandBPW Unit 3 Particulate Coal 5.00E-03 45 NO

OHMortonSaltRitt

man

B003 - Coal-Fired 

Boiler #1 Particulate Coal 5.00E-03 46 NO

MITBSimonPowe

rPlant Unit 1 Particulate Coal 5.01E-03 47 NO

PAPHGlatfelter PB1 Particulate Coal 5.21E-03 48 NO

PAPHGlatfelter PB4 Particulate Coal 5.23E-03 49 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

PAPHGlatfelter PB3 Particulate Coal 5.26E-03 50 NO

TNInvistaChattan

ooga EU002 - Boiler #4 Particulate Coal 5.30E-03 51 NO

GAIPSavannah

No. 13 Power 

Boiler - PB13 Particulate Coal 5.33E-03 52 NO

IAMuscatinePow

erandWater Unit 7 Particulate Coal 5.33E-03 53 NO

TNEastman_NO_

CBIDATA Boiler 29 Particulate Coal 5.60E-03 54 NO

IDTASCONampa

Babcock and 

Wilcox (B&W) 

#1 Particulate Coal 5.67E-03 55 NO

IDTASCONampa

Babcock and 

Wilcox (B&W) 

#2 Particulate Coal 5.67E-03 56 NO

SCSonocoHartsvi

lle Boiler Number 4 Particulate Coal 5.67E-03 57 NO

VADukeEnergyN

arrows Boiler #6 Particulate Coal 5.67E-03 58 NO

INAlcoaWarrick Unit #3 Particulate Coal 5.69E-03 59 NO

MIPharma&Upjoh

n1180 Boiler 3 Particulate Coal 5.77E-03 60 NO

VAVirginiaPolytec

hnic Boiler 7 Particulate Coal 6.00E-03 61 NO

VAPhilipMorrisPa

rk500 B3 Particulate Coal 6.00E-03 62 NO

IAADMCornProce

ssingCR EU-530 Particulate Coal 6.08E-03 63 NO

INNewEnergy Riley Boiler Particulate Coal 6.45E-03 64 NO

PAPennState 31 Particulate Coal 7.00E-03 65 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

PAPennState 32 Particulate Coal 7.00E-03 66 NO

PAPennState 34 Particulate Coal 7.00E-03 67 NO

PAPennState 35 Particulate Coal 7.00E-03 68 NO

VAPhilipMorrisPa

rk500 B2 Particulate Coal 7.33E-03 69 NO

INTateLyleSaga

more 31B1 Particulate Coal 7.33E-03 70 NO

MINeenahPaper

MI Boiler 1 Particulate Coal 7.33E-03 71 NO

WVPPGMartinsvi

lle R011-Boiler 3 Particulate Coal 7.48E-03 72 NO

VASmurfitStone

Westpt PB08 Particulate Coal 7.62E-03 73 NO

WVATKRocketC

enter

NB2766 W17479-W (Boiler 

17) Particulate Coal 7.92E-03 74 NO

WIMilwaukeePow

erPlant Boiler B21 Particulate Coal 8.00E-03 75 NO

WIWausau

# 6 Power Boiler 

(B20) Particulate Coal 8.29E-03 76 NO

NCUNCCogen ES-001 Particulate Coal 8.45E-03 77 NO

MAUMass EU#3 Particulate Coal 8.50E-03 78 NO

MAUMass EU#4 Particulate Coal 8.50E-03 79 NO

MAUMass EU#5 Particulate Coal 8.50E-03 80 NO

WIMilwaukeePow

erPlant Boiler B23 Particulate Coal 8.60E-03 81 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHBataviaTrans

missions Boiler 2 (B002) Particulate Coal 8.67E-03 82 NO

WIWausauRhine B26 Particulate Coal 8.93E-03 83 NO

WVDuPontWashi

ngtonWorks P04 Particulate Coal 9.03E-03 84 NO

IAADMCornProce

ssingCR EU-501B Particulate Coal 9.23E-03 85 NO

OHCampbellsSo

upCo B002 Particulate Coal 9.27E-03 86 NO

OHCampbellsSo

upCo B001 Particulate Coal 9.27E-03 87 NO

MNWausauPaperBrainerd EU 004 Particulate Coal 9.67E-03 88 NO

VADukeEnergyN

arrows Boiler #4 Particulate Coal 9.67E-03 89 NO

WINewPageWisconsinRapidsPower Boiler 2 - 

B20 Particulate Coal 9.83E-03 90 NO

MIGMOrion1138 EG-Boiler 3 Particulate Coal 1.00E-02 91 NO

TNOakRidge-Y12 Boiler/Unit 34 Particulate Coal 1.00E-02 92 NO

NCMillerCoors

ES-2 Coal/No. 2 

& 6 Fuel Oil 

Boiler Particulate Coal 1.03E-02 93 NO

MIHollandBPW Unit 4 Particulate Coal 1.07E-02 94 NO

WIMilwaukeePow

erPlant Boiler B22 Particulate Coal 1.07E-02 95 NO

WYSolvay

AQD #18 Boiler 

#1 Particulate Coal 1.07E-02 96 NO

NCHanesDyeWin

stonSalem ES B03 Particulate Coal 1.17E-02 97 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

COCoEnergyNati

ons Boiler 5 Particulate Coal 1.20E-02 98 NO

WIGPGreenBay2

818

B25 - Stoker 

Boiler #5 Particulate Coal 1.20E-02 99 NO

WIGPGreenBay2

818

B26 - Stoker 

Boiler #6 Particulate Coal 1.20E-02 100 NO

WIGPGreenBay2

818

B27 - Cyclone 

Boiler #7 Particulate Coal 1.20E-02 101 NO

WIGPGreenBay2

818

B28 - Stoker 

Boiler #8 Particulate Coal 1.20E-02 102 NO

MNAmericanCrys

talMoorhead Boiler 2 Particulate Coal 1.21E-02 103 NO

MSDuPontDeLisl

e1342

AF-101B (BLR1342) Particulate Coal 1.23E-02 104 NO

MSDuPontDeLisl

e1342

AF-101A (BLR1342) Particulate Coal 1.23E-02 105 NO

TNNissanSmyrna Boiler 2 Particulate Coal 1.23E-02 106 NO

TNNissanSmyrna Boiler 3 Particulate Coal 1.24E-02 107 NO

ILBungeDanville CFB Boiler Particulate Coal 1.26E-02 108 NO

MDNewPageLuke No. 25 Particulate Coal 1.26E-02 109 NO

PADomtarJohnso

nburg #81 Coal Boiler Particulate Coal 1.27E-02 110 NO

PADomtarJohnso

nburg #82 Coal Boiler Particulate Coal 1.27E-02 111 NO

MIGMDetroitHam

tramck Boiler #2 Particulate Coal 1.28E-02 112 NO

MIGMDetroitHam

tramck Boiler #3 Particulate Coal 1.28E-02 113 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MIGMDetroitHam

tramck Boiler #4 Particulate Coal 1.28E-02 114 NO

WVPPGMartinsvi

lle R072-Boiler 5 Particulate Coal 1.28E-02 115 NO

NCTysonHarmon

y TYS-ES-21 Particulate Coal 1.30E-02 116 NO

ALCargill-Decatur Keeler (S-407) Particulate Coal 1.30E-02 117 NO

COCoEnergyNati

ons Boiler 4 Particulate Coal 1.30E-02 118 NO

TNBowaterNews

print

Power Boiler No. 

3 Particulate Coal 1.30E-02 119 NO

IAADMCornProce

ssingCR EU-502A Particulate Coal 1.33E-02 120 NO

INBungeDecatur Keeler (2SP1) Particulate Coal 1.33E-02 121 NO

VAVirginiaPolytec

hnic Boiler 11 Particulate Coal 1.34E-02 122 NO

MASolutiaIncSpri

ngfield EU 150 S03 Particulate Coal 1.35E-02 123 NO

INCitizensTherm

al 15 Particulate Coal 1.40E-02 124 NO

INCitizensTherm

al 16 Particulate Coal 1.40E-02 125 NO

TNViskase Boiler 1 Particulate Coal 1.40E-02 126 NO

TNViskase Boiler 2 Particulate Coal 1.40E-02 127 NO

DEINVISTA

EU 001 - Coal 

Boiler No. 1 Particulate Coal 1.41E-02 128 NO

KYISPChemicals 0AA (Riley) Particulate Coal 1.43E-02 129 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNWausauPaperBrainerd EU 002 Particulate Coal 1.43E-02 130 NO

MNWausauPaperBrainerd EU 003 Particulate Coal 1.43E-02 131 NO

ILRockIslandArse

nal Boiler #4 Particulate Coal 1.50E-02 132 NO

TNCargillMemphi

s

Pulverized Coal 

Boiler (8301) Particulate Coal 1.50E-02 133 NO

IACargillEddyville 1.039 Particulate Coal 1.53E-02 134 NO

IACargillEddyville 1.001 Particulate Coal 1.53E-02 135 NO

IACargillEddyville 1.002 Particulate Coal 1.53E-02 136 NO

DEINVISTA

EU 003 - Coal 

Boiler No. 3 Particulate Coal 1.53E-02 137 NO

NCBlueRidgePap

er G11040 Particulate Coal 1.53E-02 138 NO

NYAESWestover Boiler 11 Particulate Coal 1.57E-02 139 NO

NYAESWestover Boiler 12 Particulate Coal 1.57E-02 140 NO

NYAESWestover Boiler 13 Particulate Coal 1.57E-02 141 NO

TNOakRidge-Y12 Boiler/Unit 32 Particulate Coal 1.57E-02 142 NO

ILRockIslandArse

nal

NBN 12888 

(Boiler #2) Particulate Coal 1.59E-02 143 NO

GAInternationalP

aperAugustaMills PB2A Particulate Coal 1.60E-02 144 NO

WYSolvay

AQD #19 Boiler 

#2 Particulate Coal 1.60E-02 145 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHRockTennCin

cinnati B001 Particulate Coal 1.63E-02 146 NO

WVDuPontWashi

ngtonWorks P06 Particulate Coal 1.64E-02 147 NO

OHAppletonIdeas Boiler 2 (B002) Particulate Coal 1.67E-02 148 NO

VADukeEnergyN

arrows Boiler #7 Particulate Coal 1.67E-02 149 NO

MDNewPageLuke No. 24 Particulate Coal 1.74E-02 150 NO

MNBlandinPaper

EnergyCtr #5 Boiler Particulate Coal 1.77E-02 151 NO

MNBlandinPaper

EnergyCtr #6 Boiler Particulate Coal 1.77E-02 152 NO

IAADMCornProce

ssingCR EU-501A Particulate Coal 1.80E-02 153 NO

WINewPageWisconsinRapidsPower Boiler 1 - 

B21 Particulate Coal 1.80E-02 154 NO

SCSmurfitStone Unit 16: Boiler #4 Particulate Coal 1.85E-02 155 NO

INAlcoaWarrick Unit #2 Particulate Coal 1.87E-02 156 NO

WVUCCSouthCh

arleston B25 Particulate Coal 1.97E-02 157 NO

SCINVISTACamd

enPlant

Unit ID 3 - Boiler 

No. 3 Particulate Coal 2.00E-02 158 NO

SCINVISTACamd

enPlant

Unit ID 4 - Boiler 

No. 4 Particulate Coal 2.00E-02 159 NO

NEADMLincoln EU26 Coal Boiler Particulate Coal 2.05E-02 160 NO

MNNorthshoreMi

ning Unit 2 (EU 002) Particulate Coal 2.06E-02 161 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

INCitizensTherm

al 12 Particulate Coal 2.07E-02 162 NO

WIDomtarNekoos

a B20 - Boiler No. 1 Particulate Coal 2.09E-02 163 NO

WIDomtarNekoos

a B21 - Boiler No. 2 Particulate Coal 2.09E-02 164 NO

WIDomtarNekoos

a B22 - Boiler No. 7 Particulate Coal 2.09E-02 165 NO

WIDomtarNekoos

a

B24 - Boiler No. 

10 Particulate Coal 2.09E-02 166 NO

WIWausauRhine B20 Particulate Coal 2.10E-02 167 NO

WIWausauRhine B21 Particulate Coal 2.10E-02 168 NO

WIWausauRhine B22 Particulate Coal 2.10E-02 169 NO

WIWausauRhine B23 Particulate Coal 2.10E-02 170 NO

VASmurfitStoneH

opewell

Combination 

Boiler Particulate Coal 2.13E-02 171 NO

ILAbbottAbbottPa

rk Unit 4AP Particulate Coal 2.13E-02 172 NO

NCMCASCherryP

oint CP-152-BOIL-01 Particulate Coal 2.17E-02 173 NO

NCMillerCoors

ES-1 Coal/No. 2 

& 6 Fuel Oil 

Boiler Particulate Coal 2.17E-02 174 NO

NCKapStone PB1 Particulate Coal 2.25E-02 175 NO

TNInvistaChattan

ooga EU002 - Boiler #3 Particulate Coal 2.33E-02 176 NO

MOIPLBlueValley Unit 1 Particulate Coal 2.35E-02 177 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILADMQuincy EU-5003 Particulate Coal 2.38E-02 178 NO

ILADMQuincy EU-5004 Particulate Coal 2.38E-02 179 NO

OHOrrvilleUtilities B005 Particulate Coal 2.43E-02 180 NO

OHUSEnrichment

CorpPiketon

X-600 Boiler No. 

3 Particulate Coal 2.47E-02 181 NO

PAHorseheadCor

pMonaco 35 Particulate Coal 2.47E-02 182 NO

MIManistiquePap

er EUBLR001 Particulate Coal 2.56E-02 183 NO

MIManistiquePap

er EUBLR002 Particulate Coal 2.56E-02 184 NO

MNAmericanCrys

talMoorhead Boiler 1 Particulate Coal 2.58E-02 185 NO

TNBowaterNews

print

Power Boiler No. 

1 Particulate Coal 2.60E-02 186 NO

GACargillGainesville B001 Particulate Coal 2.63E-02 187 NO

PAHorseheadCor

pMonaco 34 Particulate Coal 2.63E-02 188 NO

WVDuPontWashi

ngtonWorks P05 Particulate Coal 2.67E-02 189 NO

COCameoStation Unit 1 Particulate Coal 2.67E-02 190 NO

ILBungeCairo470

EU 032 (Coal 

Fired Boiler No. 

2) Particulate Coal 2.70E-02 191 NO

ILBungeCairo470

EU 032 (Coal 

Fired Boiler No.1) Particulate Coal 2.70E-02 192 NO

WIUWOshkosh 600425 Particulate Coal 2.90E-02 193 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHAkronThermal

Energy Boiler #32 (B001) Particulate Coal 2.96E-02 194 NO

MOCentralElectri

cChamois UNIT 1 Particulate Coal 2.97E-02 195 NO

MOMallinckrodt Boiler 6 Particulate Coal 3.00E-02 196 NO

WVDuPontWashi

ngtonWorks P02 Particulate Coal 3.03E-02 197 NO

OHMortonSaltRitt

man

B002 - Coal-Fired 

Boiler #2 Particulate Coal 3.07E-02 198 NO

TNOakRidge-Y12 Boiler/Unit 31 Particulate Coal 3.10E-02 199 NO

ILRockIslandArse

nal

NBN 3059 (Boiler 

#3) Particulate Coal 3.14E-02 200 NO

AZCatalystPaper

Snowflake

Power Boiler #2 

Coal Particulate Coal 3.15E-02 201 NO

MOColumbiaPow

erPlant Boiler Unit 6 Particulate Coal 3.19E-02 202 NO

MOColumbiaPow

erPlant Boiler Unit 7 Particulate Coal 3.19E-02 203 NO

MNADMMankato ASEA Boiler #5 Particulate Coal 3.20E-02 204 NO

NDAmericanCrys

talDrayton Main Boiler Particulate Coal 3.22E-02 205 NO

MNNorthshoreMi

ning Unit 1 (EU 001) Particulate Coal 3.23E-02 206 NO

VAMeadWestVac

o-CovingtonVA PWR006 Particulate Coal 3.25E-02 207 NO

VAMeadWestVac

o-CovingtonVA PWR007 Particulate Coal 3.25E-02 208 NO

VAMeadWestVac

o-CovingtonVA PWR008 Particulate Coal 3.25E-02 209 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VAMeadWestVac

o-CovingtonVA PWR009 Particulate Coal 3.25E-02 210 NO

OHUSEnrichment

CorpPiketon

X-600 Boiler No. 

1 Particulate Coal 3.33E-02 211 NO

DEINVISTA

EU 002 - Coal 

Boiler No. 2 Particulate Coal 3.36E-02 212 NO

WINewPageBiron B23 Particulate Coal 3.37E-02 213 NO

TNDuPontOldHic

koryPlant #20 Boiler Particulate Coal 3.40E-02 214 NO

MOIP&LMissouri

City Unit 1 Particulate Coal 3.46E-02 215 NO

MOIP&LMissouri

City Unit 2 Particulate Coal 3.46E-02 216 NO

WYGeneralChem

ical

GR-3-W (D 

BOILER) Particulate Coal 3.47E-02 217 NO

VADukeEnergyN

arrows Boiler #1 Particulate Coal 3.50E-02 218 NO

ALIPPineHill 109-0001-Z010 Particulate Coal 3.53E-02 219 NO

NCCampLejeune

MCB A-HP-1700-01 Particulate Coal 3.53E-02 220 NO

NCCampLejeune

MCB A-HP-1700-02 Particulate Coal 3.53E-02 221 NO

COCoEnergyNati

ons Boiler 3 Particulate Coal 3.67E-02 222 NO

NCBlueRidgePap

er G11039 Particulate Coal 3.80E-02 223 NO

SCINVISTACamd

enPlant

Unit ID 1 - Boiler 

No. 1 Particulate Coal 4.00E-02 224 NO

SCINVISTACamd

enPlant

Unit ID 2 - Boiler 

No. 2 Particulate Coal 4.00E-02 225 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCEIDuPontKinst

on ES6022B Particulate Coal 4.01E-02 226 NO

NCBlueRidgePap

er G11038 Particulate Coal 4.03E-02 227 NO

TNDuPontOldHic

koryPlant #24 Boiler Particulate Coal 4.07E-02 228 NO

MOIPLBlueValley Unit 2 Particulate Coal 4.15E-02 229 NO

INBungeDecatur B&W (1SP1) Particulate Coal 4.17E-02 230 NO

OHOrrvilleUtilities B001 Particulate Coal 4.23E-02 231 NO

OHAppletonIdeas Boiler 4 (B003) Particulate Coal 4.33E-02 232 NO

OHPainesvilleMu

nicipalElectric B004 Particulate Coal 4.33E-02 233 NO

INSABICInnovati

vePlastics

09-002 Lasker 

Boiler Particulate Coal 4.36E-02 234 NO

VAINVISTAWayn

esboro

2-205 (B#2) 

Boiler #2 Particulate Coal 4.36E-02 235 NO

VADukeEnergyN

arrows Boiler #5 Particulate Coal 4.37E-02 236 NO

GASPNewsprint PB1 Particulate Coal 4.43E-02 237 NO

OHArcelorMittalC

leveland Boiler D Particulate Coal 4.54E-02 238 NO

OHPainesvilleMu

nicipalElectric B001 Particulate Coal 4.57E-02 239 NO

GAGPSRMRiinco

n EU BO01 Particulate Coal 4.59E-02 240 NO

OHArcelorMittalC

leveland Boiler 3 Particulate Coal 4.59E-02 241 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILPrairiePowerPe

arl B1 Particulate Coal 4.66E-02 242 NO

NDMinnDakFarm

ers

Babcock and 

Wilcox Boiler #5 Particulate Coal 4.72E-02 243 NO

NCBlueRidgePap

er G11037 Particulate Coal 4.80E-02 244 NO

OHDukeEnergyG

enerationCincinn

ati

B022 (Boiler #4, 

IG-4A) Particulate Coal 4.83E-02 245 NO

WYGeneralChem

ical

GR-2-L (C 

BOILER) Particulate Coal 4.94E-02 246 NO

MNVersoPaper EU018 Bros Particulate Coal 5.00E-02 247 NO

OHBataviaTrans

missions Boiler 1 (B001) Particulate Coal 5.00E-02 248 NO

IAJohnDeereDub

uque Boiler 1 Particulate Coal 5.05E-02 249 NO

IAJohnDeereDub

uque Boiler 4 Particulate Coal 5.05E-02 250 NO

TNInvistaChattan

ooga EU002 - Boiler #5 Particulate Coal 5.07E-02 251 NO

OHBataviaTrans

missions Boiler 3 (B003) Particulate Coal 5.33E-02 252 NO

WINewPageWhiting B24 Particulate Coal 5.48E-02 253 NO

NYCornellUnivers

ity B1 Particulate Coal 5.53E-02 254 NO

INSABICInnovati

vePlastics

09-002 Erie 

Boiler Particulate Coal 5.63E-02 255 NO

OHUSEnrichment

CorpPiketon

X-600 Boiler No. 

2 Particulate Coal 5.73E-02 256 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IAJohnDeereDub

uque Boiler 2 Particulate Coal 5.84E-02 257 NO

IAJohnDeereDub

uque Boiler 3 Particulate Coal 5.84E-02 258 NO

NCMCASCherryP

oint CP-152-BOIL-02 Particulate Coal 5.97E-02 259 NO

NCCampLejeune

MCB A-HP-1700-03 Particulate Coal 6.43E-02 260 NO

NCCampLejeune

MCB A-HP-1700-04 Particulate Coal 6.43E-02 261 NO

WVPPGMartinsvi

lle R015-Boiler 4 Particulate Coal 6.47E-02 262 NO

IAAGPEagleGrov

e Boiler 1 Particulate Coal 6.51E-02 263 NO

INPurdueUniveris

ity Boiler 2 Particulate Coal 6.93E-02 264 NO

VAPhilipMorrisM

C PC Particulate Coal 7.13E-02 265 NO

OHOrrvilleUtilities B004 Particulate Coal 7.37E-02 266 NO

GACaraustar CB01 Particulate Coal 7.47E-02 267 NO

OHOrrvilleUtilities B006 Particulate Coal 7.67E-02 268 NO

IAIAStateUnivPo

werPlant B4 Particulate Coal 7.73E-02 269 NO

HIPuuneneSugar

Mill Boiler 1 Particulate Coal 7.92E-02 270 NO

HIPuuneneSugar

Mill Boiler 2 Particulate Coal 7.92E-02 271 NO

MIMISugarSebew

aing

Boiler #1 

(summer) Particulate Coal 7.93E-02 272 NO

MIMISugarSebew

aing Boiler #2 Particulate Coal 7.93E-02 273 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNRochesterUtili

ties EU003 Particulate Coal 7.98E-02 274 NO

MIMichiganSugar

Caro Boiler #1 Particulate Coal 8.27E-02 275 NO

MIMichiganSugar

Caro Boiler #2 Particulate Coal 8.27E-02 276 NO

WIDairylandPow

er-Alma Alma 1 Particulate Coal 8.40E-02 277 NO

WIDairylandPow

er-Alma Alma 2 Particulate Coal 8.40E-02 278 NO

WIDairylandPow

er-Alma Alma 3 Particulate Coal 8.40E-02 279 NO

MNRochesterUtili

ties EU001 Particulate Coal 8.43E-02 280 NO

OHPainesvilleMu

nicipalElectric B003 Particulate Coal 8.63E-02 281 NO

WINewPageKimb

erly B21 Particulate Coal 8.99E-02 282 NO

WINewPageKimb

erly B22 Particulate Coal 8.99E-02 283 NO

MIMISugarCrosw

ell

Boiler #1 (east 

Wicks) Particulate Coal 9.10E-02 284 NO

MIMISugarCrosw

ell

Boiler #2 (west 

Wicks) Particulate Coal 9.10E-02 285 NO

PABayValleyFoo

dsPittsburgh Boiler No. 3 Particulate Coal 9.30E-02 286 NO

PABayValleyFoo

dsPittsburgh Boiler No. 4 Particulate Coal 9.30E-02 287 NO

SCGaley&Lord 1EB1 Particulate Coal 9.30E-02 288 NO

SCGaley&Lord 1FB1 Particulate Coal 9.30E-02 289 NO

INTateLyleLafaye

tteSouth LA-45 Particulate Coal 1.04E-01 290 NO

NCEIDuPontKinst

on ES6022A Particulate Coal 1.09E-01 291 NO

MICargillSalt EGBOILER5 Particulate Coal 1.10E-01 292 NO

OHCityofHamilto

n B008 Particulate Coal 1.17E-01 293 NO

MOBASFHanniba

l

Coal Fired Boiler 

#4 Particulate Coal 1.22E-01 294 NO

ILDukeEnergyTu

scola Unit 1 Particulate Coal 1.30E-01 295 NO

ILDukeEnergyTu

scola Unit 3 Particulate Coal 1.30E-01 296 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IDTASCOPaul

Babcock and 

Wilcox (B&W) 

Boiler Particulate Coal 1.33E-01 297 NO

IDAmalgamatedS

ugarCoTwinFalls S-B2 Particulate Coal 1.33E-01 298 NO

GAInternationalP

aperAugustaMills PB1A Particulate Coal 1.39E-01 299 NO

MNRochesterUtili

ties EU002 Particulate Coal 1.42E-01 300 NO

MIDelphiSaginaw EUBR03 Particulate Coal 1.48E-01 301 NO

MNDESPHansO

Nyman EU002 Particulate Coal 1.57E-01 302 NO

MNDESPHansO

Nyman EU003 Particulate Coal 1.57E-01 303 NO

NYCornellUnivers

ity B8 Particulate Coal 1.70E-01 304 NO

ILAbbottNorthChi

cago

Emission Unit TT16 (Boiler #5) Particulate Coal 1.70E-01 305 NO

IDTASCOPaul Erie City Boiler Particulate Coal 1.77E-01 306 NO

PABellefieldPlant Boiler 5 Particulate Coal 1.77E-01 307 NO

WVDuPontWashi

ngtonWorks P03 Particulate Coal 1.88E-01 308 NO

ILAbbottNorthChi

cago

Emission Unit TT20 (Boiler #6) Particulate Coal 1.95E-01 309 NO

PABayValleyFoo

dsPittsburgh Boiler No. 2 Particulate Coal 2.03E-01 310 NO

PABayValleyFoo

dsPittsburgh Boiler No. 1 Particulate Coal 2.03E-01 311 NO

INNotreDame B-2 Particulate Coal 2.06E-01 312 NO

IAGrainProcessin

g Boiler #1 Particulate Coal 2.31E-01 313 NO

IAGrainProcessin

g Boiler #2 Particulate Coal 2.31E-01 314 NO

IAGrainProcessin

g Boiler #3 Particulate Coal 2.31E-01 315 NO

IAGrainProcessin

g Boiler #4 Particulate Coal 2.31E-01 316 NO

IAGrainProcessin

g Boiler #6 Particulate Coal 2.31E-01 317 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

IAGrainProcessin

g Boiler #7 Particulate Coal 2.31E-01 318 NO

MIDelphiSaginaw EUBR05 Particulate Coal 2.35E-01 319 NO

MIDelphiSaginaw EUBR04 Particulate Coal 2.43E-01 320 NO

MIPharma&Upjoh

n1178

EUEBLR43-2 

(Boiler No. 2) Particulate Coal 2.56E-01 321 NO

MOBASFHanniba

l

Coal Fired Boiler 

#5 Particulate Coal 2.59E-01 322 NO

IACentralIAPower

EP1 Unit 1 PC 

Boiler Particulate Coal 2.72E-01 323 NO

INNotreDame B-3 Particulate Coal 2.74E-01 324 NO

MOJamesRiverP

owerStation Unit 1 Particulate Coal 2.82E-01 325 NO

MOJamesRiverP

owerStation Unit 2 Particulate Coal 2.82E-01 326 NO

PABellefieldPlant Boiler 1 Particulate Coal 2.85E-01 327 NO

MIDelphiSaginaw EUBR01 Particulate Coal 2.85E-01 328 NO

MIPharma&Upjoh

n1178

EUEBLR43-4 

(Boiler No. 4) Particulate Coal 2.98E-01 329 NO

MIPharma&Upjoh

n1178

EUEBLR43-5 

(Boiler No. 5) Particulate Coal 3.08E-01 330 NO

PABellefieldPlant Boiler 3 Particulate Coal 3.15E-01 331 NO

WVDuPontWashi

ngtonWorks P01 Particulate Coal 3.17E-01 332 NO

MIDelphiSaginaw EUBR06 Particulate Coal 3.40E-01 333 NO

SCSonocoHartsvi

lle Boiler Number 3 Particulate Coal 4.10E-01 334 NO

INPurdueUniveris

ity Boiler 1 Particulate Coal 4.66E-01 335 NO

IAADMClinton

EUCOG-5 #2 

Gas Fired Boiler Particulate Gas 1 1.33E-04 1 YES

MSChevronPasc

agoula F-2103 Particulate Gas 1 2.67E-04 2 YES

IACargillEddyville 84.000 Particulate Gas 1 2.83E-04 3 YES

IACargillEddyville 86.000 Particulate Gas 1 2.83E-04 4 YES

MABostonGenera

tingMysticStation EU-17 Particulate Gas 1 3.00E-04 5 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MSDuPontDeLisl

e1342

AH-202 (BLR1342) Particulate Gas 1 3.16E-04 6 YES

IAKochNitrogen

Reformer-Aux 

Boiler Particulate Gas 1 3.58E-04 7 YES

NCCampLejeune

MCB C-AS-4151-16 Particulate Gas 1 4.20E-04 8 YES

IAGrainProcessin

g Boiler #10 Particulate Gas 1 4.29E-04 9 YES

TNValeroMemphi

s

P021 - No. 10 

Boiler Particulate Gas 1 4.33E-04 10 YES

MSChevronPasc

agoula F-8510 Particulate Gas 1 4.35E-04 11 YES

MSDuPontDeLisl

e1342

AH-101 (BLR1342) Particulate Gas 1 4.49E-04 12 YES

MDUofMaryland EU 001-4 Particulate Gas 1 4.98E-04 13 YES

TNValeroMemphi

s

P044-DHT 18 

Stripper Reboiler 

Heater Particulate Gas 1 5.50E-04 14 YES

TNValeroMemphi

s

P043 - DHT 18 

Reactor Feed 

Heater Particulate Gas 1 5.67E-04 15 YES

NJSunocoWestvil

le Boiler #7 Particulate Gas 1 6.00E-04 16 YES

NJSunocoWestvil

le Boiler #6 Particulate Gas 1 6.22E-04 17 YES

NJSunocoWestvil

le Boiler #5 Particulate Gas 1 6.23E-04 18 YES

KSCoffeyvilleRefi

nery EU-39-FH0027 Particulate Gas 1 6.23E-04 19 NO

NJSunocoWestvil

le H-1 LSG Particulate Gas 1 6.54E-04 20 NO

NJSunocoWestvil

le Boiler #8 Particulate Gas 1 6.57E-04 21 NO

TNValeroMemphi

s

P021 - No. 9 

Boiler Particulate Gas 1 7.00E-04 22 NO

TNValeroMemphi

s

P037 - SHU 

Splitter Reboiler 

Heater Particulate Gas 1 8.00E-04 23 NO

SCMichelinSandy

Springs B:02:01 Particulate Gas 1 8.92E-04 24 NO

MNADMCornDivi

sion

Gas Boiler #4 

EU054 Particulate Gas 1 9.00E-04 25 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHSolaeBellvue B008 Particulate Gas 1 9.76E-04 26 NO

LAValeroRefining 401E Boiler Particulate Gas 1 1.00E-03 27 NO

LAValeroRefining GDU Heater Particulate Gas 1 1.00E-03 28 NO

LAValeroRefining

SMR1 Heater No. 

1 Particulate Gas 1 1.00E-03 29 NO

WATransAltaCen

tralia

EU 12 BHP 

Auxiliary Boiler Particulate Gas 1 1.00E-03 30 NO

NJSunocoWestvil

le PH-2 CRU Particulate Gas 1 1.03E-03 31 NO

NJSunocoWestvil

le 2H-202 ULSD Particulate Gas 1 1.11E-03 32 NO

NJSunocoWestvil

le PH-6 CRU Particulate Gas 1 1.29E-03 33 NO

NJSunocoWestvil

le HH-1 HTU Particulate Gas 1 1.34E-03 34 NO

MSDuPontDeLisl

e1342

AF-103 (BLR1342) Particulate Gas 1 1.35E-03 35 NO

NJHessCorpPortReading U4 - Boiler #4 Particulate Gas 1 1.35E-03 36 NO

NJSunocoWestvil

le PH-1 ISOM Particulate Gas 1 1.35E-03 37 NO

MSDuPontDeLisl

e1342

AH-201 (BLR1342) Particulate Gas 1 1.35E-03 38 NO

NJSunocoWestvil

le B-5A FCCU Particulate Gas 1 1.43E-03 39 NO

NJSunocoWestvil

le B-5B FCCU Particulate Gas 1 1.43E-03 40 NO

MDUofMaryland EU 001-8 Particulate Gas 1 1.46E-03 41 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

INTateLyleSaga

more 21B501 Particulate Gas 1 1.52E-03 42 NO

NJSunocoWestvil

le B-301 POLY Particulate Gas 1 1.62E-03 43 NO

NJSunocoWestvil

le HA-4 VPS Particulate Gas 1 1.62E-03 44 NO

PASunocoPhilad

elphia CU-138 Particulate Gas 1 1.66E-03 45 NO

MNStPaulParkRe

f EU 028 Particulate Gas 1 1.67E-03 46 NO

LACitgoLakeChar

les EQT238 Particulate Gas 1 1.67E-03 47 NO

MNStPaulParkRe

f EU 029 Particulate Gas 1 1.67E-03 48 NO

SCMarlboroPape

r Package Boiler Particulate Gas 1 1.67E-03 49 NO

TXTotalPetroche

mPortArthur 51DHT1H-1 Particulate Gas 1 1.67E-03 50 NO

MSChevronPasc

agoula F-8400 Particulate Gas 1 1.69E-03 51 NO

SCEastmanColo

mbia

HTM Heater #3 

(Equip ID 1101) Particulate Gas 1 1.73E-03 52 NO

LAValeroRefining F-15-05 Particulate Gas 1 2.00E-03 53 NO

LAValeroRefining

KHT Heater F-33-

05 Particulate Gas 1 2.00E-03 54 NO

KYCatlettsburgR

efining 1-9-B-588 Particulate Gas 1 2.07E-03 55 NO

MSChevronPasc

agoula F-6531 Particulate Gas 1 2.09E-03 56 NO

NJSunocoWestvil

le B-3 FCCU Particulate Gas 1 2.21E-03 57 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXDiamondSham

rockMcKee

B-12 (600# 

Boiler) Particulate Gas 1 2.23E-03 58 NO

LAValeroRefining F-72-703 Particulate Gas 1 2.33E-03 59 NO

TXTotalPetroche

mPortArthur 52DHT2H-1 Particulate Gas 1 2.33E-03 60 NO

NJSunocoWestvil

le HA-3B VPS Particulate Gas 1 2.36E-03 61 NO

NJHessCorpPortReading U4 - Boiler #3 Particulate Gas 1 2.38E-03 62 NO

MSChevronPasc

agoula F-8300B Particulate Gas 1 2.43E-03 63 NO

PASunocoPhilad

elphia CU-137 Particulate Gas 1 2.49E-03 64 NO

OKTerraNitrogen

#1 Primary 

Reformer Particulate Gas 1 2.50E-03 65 NO

KYDomtarHawes

ville

Package Boiler C40 Particulate Gas 1 2.52E-03 66 NO

MSChevronPasc

agoula F-8120 Particulate Gas 1 2.56E-03 67 NO

NJSunocoWestvil

le 2H-201 ULSD Particulate Gas 1 2.70E-03 68 NO

NJSunocoWestvil

le HA-03A VPS Particulate Gas 1 2.71E-03 69 NO

NJSunocoWestvil

le H-2 LSG Particulate Gas 1 2.72E-03 70 NO

NJSunocoWestvil

le HA-01 VPS Particulate Gas 1 2.75E-03 71 NO

MSChevronPasc

agoula F-1601 Particulate Gas 1 2.78E-03 72 NO

NJSunocoWestvil

le

HC-301 

Claytreater Particulate Gas 1 2.90E-03 73 NO

LAValeroRefining

SMR1 Heater No. 

2 Particulate Gas 1 3.00E-03 74 NO

MNStPaulParkRe

f EU 026 Particulate Gas 1 3.00E-03 75 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MSWeyerhaeuse

rColumbus AA-019 Particulate Gas 1 3.00E-03 76 NO

NJSunocoWestvil

le PH-5B CRU Particulate Gas 1 3.02E-03 77 NO

MSChevronPasc

agoula F-8110 Particulate Gas 1 3.13E-03 78 NO

TXDiamondSham

rockThreeRivers H-201 Particulate Gas 1 3.17E-03 79 NO

TXDiamondSham

rockThreeRivers H-203 Particulate Gas 1 3.17E-03 80 NO

TXDiamondSham

rockThreeRivers H-204 Particulate Gas 1 3.17E-03 81 NO

WIWisconsinPap

erboard2879 B24 Particulate Gas 1 3.29E-03 82 NO

MSChevronPasc

agoula F-8620 Particulate Gas 1 3.49E-03 83 NO

TXTotalPetroche

mPortArthur 52DHT2H-2 Particulate Gas 1 3.50E-03 84 NO

LAValeroRefining H-60-1 Particulate Gas 1 3.67E-03 85 NO

LAValeroRefining H-60-2 Particulate Gas 1 3.67E-03 86 NO

LAValeroRefining H-60-3 Particulate Gas 1 3.67E-03 87 NO

LAValeroRefining H-60-4 Particulate Gas 1 3.67E-03 88 NO

MSChevronPasc

agoula F-6101 Particulate Gas 1 3.88E-03 89 NO

MSChevronPasc

agoula F-6102 Particulate Gas 1 3.88E-03 90 NO

MSChevronPasc

agoula F-8300C Particulate Gas 1 3.94E-03 91 NO

TXTotalPetroche

mPortArthur 51DHT1H-3 Particulate Gas 1 4.00E-03 92 NO

OHSolaeBellvue B010 Particulate Gas 1 4.23E-03 93 NO

CTCytecWallingf

ord 150 Furnace Particulate Gas 1 4.33E-03 94 NO

MSMasoniteLaur

el BB-001 Particulate Gas 1 4.33E-03 95 NO

DEPremcorGroup

Valero Boiler 1 Particulate Gas 1 4.40E-03 96 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNStPaulParkRe

f EU 007 Particulate Gas 1 4.67E-03 97 NO

MSChevronPasc

agoula F-8130 Particulate Gas 1 4.76E-03 98 NO

MSChevronPasc

agoula F-8300A Particulate Gas 1 5.15E-03 99 NO

WVWeyerhaeuse

rBuckhannon 001-02 Particulate Gas 1 5.54E-03 100 NO

LACitgoLakeChar

les EQT237 Particulate Gas 1 5.67E-03 101 NO

WAGraysHarbor

Paper

No. 9 Boiler 

(EU3) Particulate Gas 1 5.81E-03 102 NO

NJSunocoWestvil

le PH-4A CRU Particulate Gas 1 5.96E-03 103 NO

NJSunocoWestvil

le PH-3 CRU Particulate Gas 1 5.98E-03 104 NO

NJSunocoWestvil

le PH-4B CRU Particulate Gas 1 5.98E-03 105 NO

TXDiamondSham

rockThreeRivers 100-H2 Particulate Gas 1 6.00E-03 106 NO

KYDomtarHawes

ville

No. 2 Backup 

Boiler C-50 Particulate Gas 1 7.03E-03 107 NO

TXValeroPortArth

ur 942 F1300 Particulate Gas 1 7.72E-03 108 NO

TXValeroPortArth

ur 942 F2000 Particulate Gas 1 7.72E-03 109 NO

TXValeroPortArth

ur 942 F1000 Particulate Gas 1 7.72E-03 110 NO

MSChevronPasc

agoula F-2440 Particulate Gas 1 8.09E-03 111 NO

MSChevronPasc

agoula F-2450 Particulate Gas 1 8.09E-03 112 NO

MSChevronPasc

agoula F-2460 Particulate Gas 1 8.09E-03 113 NO

MSChevronPasc

agoula F-2470 Particulate Gas 1 8.09E-03 114 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MSChevronPasc

agoula F-2480 Particulate Gas 1 8.09E-03 115 NO

MSChevronPasc

agoula F-2490 Particulate Gas 1 8.09E-03 116 NO

MSChevronPasc

agoula F-6250 Particulate Gas 1 8.38E-03 117 NO

TXDiamondSham

rockThreeRivers H-1102 Particulate Gas 1 8.43E-03 118 NO

MNStPaulParkRe

f EU 005 Particulate Gas 1 8.90E-03 119 NO

TXDiamondSham

rockThreeRivers H-1402 Particulate Gas 1 9.00E-03 120 NO

MDUofMaryland EU 001-2 Particulate Gas 1 9.35E-03 121 NO

PASunocoMarcu

sHook

040 (10-4 Feed 

Heater) Particulate Gas 1 9.77E-03 122 NO

MNStPaulParkRe

f EU 001 Particulate Gas 1 1.00E-02 123 NO

MNStPaulParkRe

f EU 011 Particulate Gas 1 1.00E-02 124 NO

MNStPaulParkRe

f EU 013 Particulate Gas 1 1.00E-02 125 NO

MNStPaulParkRe

f EU 023 Particulate Gas 1 1.00E-02 126 NO

MNStPaulParkRe

f EU 024 Particulate Gas 1 1.00E-02 127 NO

TXDiamondSham

rockThreeRivers 100-H1 Particulate Gas 1 1.03E-02 128 NO

DEPremcorGroup

Valero Boiler 3 Particulate Gas 1 1.10E-02 129 NO

GAADMLocation

551

640- Cleaver 

Brooks Particulate Gas 1 1.18E-02 130 NO

MNStPaulParkRe

f EU 025 Particulate Gas 1 1.20E-02 131 NO

MNStPaulParkRe

f EU 006 Particulate Gas 1 1.33E-02 132 NO

DEPremcorGroup

Valero Boiler 2 Particulate Gas 1 1.40E-02 133 NO

IAAlcoaDavenpor

t CFRN21 Particulate Gas 1 1.55E-02 134 NO

MNStPaulParkRe

f EU 010 Particulate Gas 1 1.67E-02 135 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNStPaulParkRe

f EU 027 Particulate Gas 1 2.33E-02 136 NO

MNStPaulParkRe

f EU 014 Particulate Gas 1 3.67E-02 137 NO

DEPremcorGroup

Valero Boiler 4 Particulate Gas 1 4.80E-02 138 NO

TXEastmanChem

Longview UD030B11 Particulate Gas 1 7.19E-02 139 NO

TXMeadWestvac

oEvadale 21-2069 Particulate Gas 1 7.80E-02 140 NO

MNStPaulParkRe

f EU 002 Particulate Gas 1 8.00E-02 141 NO

MNStPaulParkRe

f EU 015 Particulate Gas 1 8.00E-02 142 NO

MTExxonMobilBill

ings KCOB Particulate Gas 1 2.53E-01 143 NO

INArcelorMittalBu

rnsHarbor

Hot Dip Coating 

Line Annealing 

Furnace Particulate Gas 1 4.78E-06 yes 1 YES

INNucorSteel

Cold Mill 

Annealing Particulate Gas 1 1.04E-03 yes 2 YES

CORockyMtnSte

el212

Rod/Bar Mill 

Furnace 

95OPPB088 Particulate Gas 1 1.38E-03 yes 3 NO

UTWestinghouse 202 Particulate Gas 1 2.59E-03 yes 4 NO

ILUSSGraniteCity

No. 8 Galvanizing 

Line Furnace Particulate Gas 1 3.28E-03 yes 5 NO

INOutokumpuStai

nlessPlate

Heppenstall 

Annealing 

Furnace Particulate Gas 1 3.33E-03 yes 6 NO

IAAlcoaDavenpor

t TFRN16 Particulate Gas 1 1.15E-02 yes 7 NO

INAlcoaWarrick

Annealing 

Furnace #15 Particulate Gas 1 2.93E-02 yes 8 NO

INAlcoaWarrick

Pre-Heat Furnace 

#36 Particulate Gas 1 2.93E-02 yes 9 NO

LAShellChemica

Geismar Furnace F-S801 Particulate Gas 2 4.20E-04 1 YES

WIGPGreenBay2

818

B29 - Fluidized 

Bed Boiler #9 Particulate Gas 2 7.90E-04 2 YES

SCBMWManufac

turingCo HB03 Particulate Gas 2 1.38E-03 3 NO

INTateLyleSaga

more 21B501 Particulate Gas 2 1.43E-03 4 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MDSeverstalSpar

rows

1BLR (No. 1 

Boiler) Particulate Gas 2 4.47E-03 5 NO

WVMountainStat

eCarbonFollansb

ee S1 Particulate Gas 2 6.10E-03 6 NO

KYAKSteelWestWorks No. 13 Boiler Particulate Gas 2 8.67E-03 7 NO

INArcelorMittalBu

rnsHarbor No. 7 Boiler Particulate Gas 2 8.87E-03 8 NO

GAGPSRMRiinco

n EU BO02 Particulate Gas 2 1.09E-02 9 NO

KYAKSteelWestWorks No. 7 Boiler Particulate Gas 2 1.67E-02 10 NO

PAUSSClairton B002 Boiler No. 2 Particulate Gas 2 1.72E-02 11 NO

KYAKSteelWestWorks No. 6 Boiler Particulate Gas 2 2.13E-02 12 NO

KYAKSteelWestWorks No. 5 Boiler Particulate Gas 2 2.60E-02 13 NO

PAUSSMonValle

yIrvin

Terne Line Lead 

Pot Particulate Gas 2 3.06E-01 yes

TNMilanArmyAm

munitionPlant

D88L-1, Source 

#27-0010-86 Particulate Liquid 5.11E-04 1 YES

SCGPChemRuss

ellville FO Boiler Particulate Liquid 6.00E-04 2 YES

NJSunocoWestvil

le Boiler #8 Particulate Liquid 6.78E-04 3 YES

PAConemaughP

owerPlantNewFlo

rence Aux Boiler B Particulate Liquid 8.73E-04 4 YES

NJSunocoWestvil

le Boiler #6 Particulate Liquid 1.02E-03 5 YES

PACherokeePhar

m

SG-C, Title V 

Source ID 037 Particulate Liquid 1.60E-03 6 YES

NJSunocoWestvil

le Boiler #7 Particulate Liquid 1.72E-03 7 YES

PACherokeePhar

m

SG-B, Title V 

Source ID 036 Particulate Liquid 1.80E-03 8 YES

NJSunocoWestvil

le Boiler #5 Particulate Liquid 1.82E-03 9 YES

ALBP-Decatur24 AB-8301 Particulate Liquid 2.30E-03 10 YES

MANewarkAmeri

ca Boiler #2 Particulate Liquid 2.50E-03 11 NO

SCCogenSouth

B002 - Auxiliary 

Boiler #1 Particulate Liquid 3.05E-03 12 NO

SCCogenSouth

B003 - Auxiliary 

Boiler #2 Particulate Liquid 3.05E-03 13 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

SCCogenSouth

B004 - Auxiliary 

Boiler #3 Particulate Liquid 3.05E-03 14 NO

SCMitsubishiPoly

esterFilm

Dowtherm Heater 

4 

(4FPDDOWHSA) Particulate Liquid 3.32E-03 15 NO

MIConsumerEner

gyCo-Campbell EUAUXBLR12 Particulate Liquid 3.37E-03 16 NO

MNMinnesotaSoy

beanProcessors Boiler 1 EU026 Particulate Liquid 3.77E-03 17 NO

MNMinnesotaSoy

beanProcessors Boiler 2 EU027 Particulate Liquid 3.77E-03 18 NO

WIWisconsinPap

erboard2879 B24 Particulate Liquid 4.10E-03 19 NO

VAAltavistaPower

Station Unit No. 003 Particulate Liquid 4.92E-03 20 NO

GAGPCelluloseB

runswick

U707 -- No. 7 

Power Boiler Particulate Liquid 5.23E-03 21 NO

OHSolaeBellvue B010A Particulate Liquid 5.43E-03 22 NO

SCDAKAmericas P8E Particulate Liquid 6.51E-03 23 NO

PAConemaughP

owerPlantNewFlo

rence Aux Boiler A Particulate Liquid 7.47E-03 24 NO

GAGPCelluloseB

runswick

U706 -- No. 6 

Power Boiler Particulate Liquid 8.27E-03 25 NO

SCDAKAmericas P8D Particulate Liquid 9.04E-03 26 NO

TNInvistaChattan

ooga

EU003 - 

Vaporizer #2 Particulate Liquid 9.40E-03 27 NO

WYSinclairCaspe

r

Pt. 9 B-1 #4 

Crude Heater Particulate Liquid 1.03E-02 28 NO

SCDAKAmericas P8C Particulate Liquid 1.03E-02 29 NO

MNGPDuluth EU33 Boiler #3 Particulate Liquid 1.10E-02 30 NO

ALGPBrewtonMill

BR-PSG0-S018 

No. 1 Power 

Boiler Particulate Liquid 1.23E-02 31 NO

INUSSteelGaryW

orks O4B10459 Particulate Liquid 1.52E-02 32 NO

NCDomtar

66-25-2050 (No. 

1 Package Boiler) Particulate Liquid 1.61E-02 33 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NYConEd59thSt

StationNewYork Boiler 118 Particulate Liquid 1.75E-02 34 NO

PABoeingRidleyP

ark 033 Particulate Liquid 1.83E-02 35 NO

FLOkeelanta268 Boiler No. 16 Particulate Liquid 1.83E-02 36 NO

MAUMass EU#7 Particulate Liquid 1.88E-02 37 NO

MENewPageRumford PB#3 Particulate Liquid 2.00E-02 38 NO

MNStPaulParkRe

f EU 021 Particulate Liquid 2.33E-02 39 NO

NJVinelandMuniE

lectricHowardDown Unit 9 Particulate Liquid 2.41E-02 40 NO

MDUofMaryland EU 001-4 Particulate Liquid 2.98E-02 41 NO

MENewPageRumford PB#5 Particulate Liquid 3.00E-02 42 NO

MNStPaulParkRe

f EU 020 Particulate Liquid 3.00E-02 43 NO

WANipponPaper

#10 Package 

Boiler Particulate Liquid 3.06E-02 44 NO

MDMirantChalkP

oint Unit 4 Particulate Liquid 3.43E-02 45 NO

MNStPaulParkRe

f EU 018 Particulate Liquid 3.67E-02 46 NO

NCWeyerhaeuse

r-Vanceboro ES 161-001 Particulate Liquid 3.70E-02 47 NO

ORCascadePacifi

cPulp PB1EU Particulate Liquid 4.03E-02 48 NO

WANipponPaper

#9 Package 

Boiler Particulate Liquid 4.11E-02 49 NO

OHCampbellsSo

upCo B003 Particulate Liquid 4.30E-02 50 NO

ORGeorgiaPacifi

cWaunaMill

EU33 - Power 

Boiler Particulate Liquid 4.41E-02 51 NO

OHCampbellsSo

upCo B004 Particulate Liquid 4.90E-02 52 NO

MAGEAviationLy

nn 99-2 Particulate Liquid 5.50E-02 53 NO

MAGEAviationLy

nn 99-1 Particulate Liquid 5.67E-02 54 NO

NYDMVInternatio

nal BOIL1 Particulate Liquid 5.67E-02 55 NO

NYDMVInternatio

nal BOIL2 Particulate Liquid 5.67E-02 56 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

SCDAKAmericas P8F Particulate Liquid 5.67E-02 57 NO

MAGEAviationLy

nn 99-5 Particulate Liquid 5.80E-02 58 NO

ORWahChang

6633-78 (SEP-AS502B, Boiler #2) Particulate Liquid 6.49E-02 59 NO

MAGEAviationLy

nn 99-3 Particulate Liquid 6.70E-02 60 NO

MEFPLEnergyWy

man Unit #5 Particulate Liquid 6.97E-02 61 NO

VASmurfitStone

Westpt PB08 Particulate Liquid 7.21E-02 62 NO

MEPioneerPlastic

s Boiler #6 Particulate Liquid 7.33E-02 63 NO

MEVersoPaperA

ndroscoggin

Power Boiler No. 

1 Particulate Liquid 7.97E-02 64 NO

MEVersoPaperA

ndroscoggin

Power Boiler No. 

2 Particulate Liquid 7.97E-02 65 NO

MNStPaulParkRe

f EU 003 Particulate Liquid 8.00E-02 66 NO

MNStPaulParkRe

f EU 016 Particulate Liquid 8.00E-02 67 NO

OHGEAviationEv

endale EA-019-D Particulate Liquid 8.00E-02 68 NO

OHGEAviationEv

endale EA-019-C Particulate Liquid 9.67E-02 69 NO

MNStPaulParkRe

f EU 009 Particulate Liquid 1.10E-01 70 NO

CTElectric Boat EMU 17 Particulate Liquid 1.27E-01 71 NO

MDUofMaryland EU 001-2 Particulate Liquid 1.29E-01 72 NO

OHGEAviationEv

endale EA-019-B Particulate Liquid 1.33E-01 73 NO

NCWeyerhaeuse

r-Vanceboro ES 150-001 Particulate Liquid 1.41E-01 74 NO

WYSinclairWyom

ing Pt 40 #8 HPB Particulate Liquid 1.55E-01 75 NO

WYSinclairWyom

ing Pt 41 #9 HPB Particulate Liquid 1.69E-01 76 NO

NCKapStone PKG2 Particulate Liquid 1.70E-01 77 NO

SCBowaterCoate

dPaper Power Boiler Particulate Liquid 1.83E-01 78 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 3-PM Floor

FacilityID

CombustorID_co

mmon

Pollutant_

Name

MACT 

Floor 

FuelCat lb/mmBtu

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MEPioneerPlastic

s Boiler #4 Particulate Liquid 2.00E-01 79 NO

NCInvistaHwy421 B7600 Particulate Liquid 2.27E-01 80 NO

VANewportNews

ShipbuildingDryD

ock 78-E1 Particulate Liquid 4.50E-01 81 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

CORockyMtnSte

el212

Rod/Bar Mill 

Furnace 

95OPPB088 CO 5.03E-01 Gas 1 yes 1 YES

MDSeverstalSpa

rrows

CRM Batch 

Annealing 

Furnaces CO 1.35E+00 Gas 1 yes 2 YES

UTWestinghous

e 202 CO 1.39E+01 Gas 1 yes 3 NO

NYArcelorMittal

Hot Dip 

Galvanizing 

Despatch 

Furnace CO 2.42E+01 Gas 1 yes 4 NO

INAlcoaWarrick

Annealing 

Furnace #15 CO 2.80E+01 Gas 1 yes 5 NO

INAlcoaWarrick

Pre-Heat 

Furnace #36 CO 2.80E+01 Gas 1 yes 6 NO

IAAlcoaDavenpo

rt PFRN04 CO 4.69E+01 Gas 1 yes 7 NO

MDSeverstalSpa

rrows

Box Annealing 

Furnaces CO 7.17E+01 Gas 1 yes 8 NO

INOutokumpuSt

ainlessPlate

Heppenstall 

Annealing 

Furnace CO 8.74E+01 Gas 1 yes 9 NO

IAAlcoaDavenpo

rt PFRN03 CO 1.09E+02 Gas 1 yes 10 NO

ILUSSGraniteCit

y

No. 8 

Galvanizing Line 

Furnace CO 1.44E+02 Gas 1 yes 11 NO

INArcelorMittalB

urnsHarbor

Hot Dip Coating 

Line Annealing 

Furnace CO 1.46E+02 Gas 1 yes 12 NO

WICharterSteel P31 CO 3.05E+02 Gas 1 yes 13 NO

WVAlcanRavens

wood

Salem 12-Zone 

Heat Treat 

(008P102) CO 1.25E+03 Gas 1 yes 14 NO

OKVRCOklahom

a H-101 CO 9.36E-03 Gas 1 1 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OKVRCOklahom

a H-102A CO 1.01E-02 Gas 1 2 YES

TXRohmHaasDe

erPark ACET-2B-4 CO 1.33E-02 Gas 1 3 YES

OKConocoPhillip

sPoncaCity H-9902 CO 2.00E-02 Gas 1 4 YES

TXDiamondSha

mrockThreeRive

rs H-201 CO 2.71E-02 Gas 1 5 YES

TXDiamondSha

mrockThreeRive

rs H-203 CO 2.71E-02 Gas 1 6 YES

TXDiamondSha

mrockThreeRive

rs H-204 CO 2.71E-02 Gas 1 7 YES

VAWesternRefin

ingYorktown F-562 CO 3.94E-02 Gas 1 8 YES

OKConocoPhillip

sPoncaCity H-9851 CO 4.00E-02 Gas 1 9 YES

INBPWhitingRefi

nery B-601 CO 4.33E-02 Gas 1 10 YES

OKConocoPhillip

sPoncaCity H-0016 CO 4.33E-02 Gas 1 11 YES

TXOccidentalCh

emGregory

VCM Plant 1 

Furnace 1 CO 5.02E-02 Gas 1 12 YES

TXOccidentalCh

emGregory

VCM Plant 1 

Furnace 2 CO 5.02E-02 Gas 1 13 YES

TXOccidentalCh

emGregory

VCM Plant 1 

Furnace 3 CO 5.02E-02 Gas 1 14 YES

TXOccidentalCh

emGregory

VCM Plant 1 

Furnace 4 CO 5.02E-02 Gas 1 15 YES

MSChevronPasc

agoula F-2103 CO 5.41E-02 Gas 1 16 YES

TXDiamondSha

mrockThreeRive

rs H-1102 CO 6.32E-02 Gas 1 17 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NJSunocoWestv

ille Boiler #8 CO 6.58E-02 Gas 1 18 YES

KYCatlettsburgR

efining 2-23-B-4 CO 7.75E-02 Gas 1 19 YES

ILWoodRiverRefi

nery HTR-DU1-F302 CO 7.88E-02 Gas 1 20 YES

PASunocoMarcu

sHook

705 (12-4 LSG 

Heater, H01) CO 8.00E-02 Gas 1 21 YES

OKVRCOklahom

a H-201 CO 8.65E-02 Gas 1 22 YES

LACitgoLakeCha

rles EQT242 CO 8.95E-02 Gas 1 23 YES

INNucorSteel

Cold Mill 

Annealing CO 9.01E-02 Gas 1 24 YES

MSChevronPasc

agoula F-6701 CO 9.35E-02 Gas 1 25 YES

KYCatlettsburgR

efining 2-122-B-1 CO 9.92E-02 Gas 1 26 YES

ALHuntRefining HS-2041A CO 1.00E-01 Gas 1 27 YES

ALHuntRefining HS-2041B CO 1.00E-01 Gas 1 28 YES

ALHuntRefining HS-2041C CO 1.00E-01 Gas 1 29 YES

OKConocoPhillip

sPoncaCity H-0003 CO 1.00E-01 Gas 1 30 YES

TXAirProductsB

aytown BOILER (EPN 7) CO 1.00E-01 Gas 1 31 YES

TXChevronBayto

wn H-1001 CO 1.00E-01 Gas 1 32 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXEquistarPasa

dena Boiler (P-25) CO 1.00E-01 Gas 1 33 YES

TXValeroTexasC

ity Heater 13-1451 CO 1.00E-01 Gas 1 34 YES

TXValeroTexasC

ity Heater 16 CO 1.00E-01 Gas 1 35 YES

TXValeroTexasC

ity Heater 17 CO 1.00E-01 Gas 1 36 YES

TXValeroTexasC

ity Heater 28 CO 1.00E-01 Gas 1 37 YES

TXValeroTexasC

ity Heater 35 CO 1.00E-01 Gas 1 38 YES

TXValeroTexasC

ity Heater 44 CO 1.00E-01 Gas 1 39 YES

LAWestlakeStyr

ene 1-90 CO 1.01E-01 Gas 1 40 YES

OREvrazOregon

Steel

EU-5 Vacuum 

Degasser Boiler CO 1.02E-01 Gas 1 41 YES

LALakeCharlesC

hemical

LAB-LH-1 (Pacol 

Charge Heater) CO 1.02E-01 Gas 1 42 YES

TXValeroTexasC

ity Heater 45 CO 1.08E-01 Gas 1 43 YES

MSChevronPasc

agoula F-8400 CO 1.10E-01 Gas 1 44 YES

TXValeroTexasC

ity Heater 46 CO 1.10E-01 Gas 1 45 YES

KYCatlettsburgR

efining 2-30-B-1 CO 1.16E-01 Gas 1 46 YES

LAShellChemica

Geismar

Furnace FS2801 CO 1.18E-01 Gas 1 47 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

KYCatlettsburgR

efining 2-23-B-3 CO 1.18E-01 Gas 1 48 YES

TXRohmHaasDe

erPark N-13 CO 1.20E-01 Gas 1 49 YES

TXWesternRefini

ng F-4150 CO 1.22E-01 Gas 1 50 YES

TXWesternRefini

ng F-4160 CO 1.22E-01 Gas 1 51 YES

TXValeroTexasC

ity Heater 57 CO 1.27E-01 Gas 1 52 YES

MSChevronPasc

agoula F-2440 CO 1.28E-01 Gas 1 53 YES

MSChevronPasc

agoula F-2450 CO 1.28E-01 Gas 1 54 YES

MSChevronPasc

agoula F-2460 CO 1.28E-01 Gas 1 55 YES

MSChevronPasc

agoula F-2470 CO 1.28E-01 Gas 1 56 YES

MSChevronPasc

agoula F-2480 CO 1.28E-01 Gas 1 57 YES

MSChevronPasc

agoula F-2490 CO 1.28E-01 Gas 1 58 YES

WAConocoPhilli

psFerndale 38F-101 CO 1.29E-01 Gas 1 59 YES

TXValeroTexasC

ity Heater 58 CO 1.29E-01 Gas 1 60 YES

TXRohmHaasDe

erPark ACET-2B-1 CO 1.30E-01 Gas 1 61 YES

TXValeroTexasC

ity Heater 18 CO 1.33E-01 Gas 1 62 YES

TXValeroTexasC

ity Heater 19 CO 1.33E-01 Gas 1 63 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXValeroTexasC

ity Heater 20 CO 1.33E-01 Gas 1 64 YES

TXValeroTexasC

ity Heater 21 CO 1.33E-01 Gas 1 65 YES

TXValeroTexasC

ity Heater 22 CO 1.33E-01 Gas 1 66 YES

TXValeroTexasC

ity Heater 23 CO 1.33E-01 Gas 1 67 YES

TXWesternRefini

ng H-8801 CO 1.33E-01 Gas 1 68 YES

TXWesternRefini

ng H-8802 CO 1.33E-01 Gas 1 69 YES

IAADMClinton

EUCOG-5 #2 

Gas Fired Boiler CO 1.35E-01 Gas 1 70 YES

TXDeerParkRefi

nery H31003 CO 1.35E-01 Gas 1 71 YES

TXDeerParkRefi

nery H5104 CO 1.35E-01 Gas 1 72 YES

TXLyondellPasa

dena B-1751 CO 1.35E-01 Gas 1 73 YES

TXLyondellPasa

dena B-2890 CO 1.35E-01 Gas 1 74 YES

TXLyondellPasa

dena B-801 CO 1.35E-01 Gas 1 75 YES

TXWesternRefini

ng F-1602 CO 1.35E-01 Gas 1 76 YES

TXRohmHaasDe

erPark HT-49 CO 1.40E-01 Gas 1 77 YES

TXRohmHaasDe

erPark N-12 CO 1.40E-01 Gas 1 78 YES

LAShellChemica

Geismar Furnace F-S801 CO 1.40E-01 Gas 1 79 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

DEDuPontEdge

moor RX-9 CO 1.40E-01 Gas 1 80 YES

PANorfolkSouth

ern Boiler 1 CO 1.50E-01 Gas 1 81 YES

TXWesternRefini

ng 109 CO 1.57E-01 Gas 1 82 YES

TXRohmHaasDe

erPark ACET-2A-1 CO 1.67E-01 Gas 1 83 YES

TXValeroCorpus

Christi 154-H-1 CO 1.67E-01 Gas 1 84 YES

MSChevronPasc

agoula F-6410 CO 1.68E-01 Gas 1 85 YES

KYCatlettsburgR

efining 2-36-B-1 CO 1.69E-01 Gas 1 86 YES

OKConocoPhillip

sPoncaCity H-0048 CO 1.70E-01 Gas 1 87 YES

MTMontanaRefi

ning

H-1801 

Hydrogen Plant 

Heater CO 1.71E-01 Gas 1 88 YES

TXRohmHaasDe

erPark ACET-2A-3 CO 1.77E-01 Gas 1 89 YES

MSChevronPasc

agoula F-8300B CO 1.84E-01 Gas 1 90 YES

VAUniversityofVi

rginia 7103-1-01R CO 1.95E-01 Gas 1 91 YES

WAUSOilandRef

iningTacoma H-3 CO 2.00E-01 Gas 1 92 NO

TXEquistarChan

nelview F4360 CO 2.03E-01 Gas 1 93 NO

TXValeroCorpus

Christi 169-B-5 CO 2.07E-01 Gas 1 94 NO

ORGeorgiaPacifi

cWaunaMill

EU33 - Power 

Boiler CO 2.09E-01 Gas 1 95 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OKTerraInternati

onalWoodward

Primary 

Reformer H2030 CO 2.19E-01 Gas 1 96 NO

LACitgoLakeCha

rles EQT032 CO 2.23E-01 Gas 1 97 NO

TXWesternRefini

ng F-4170 CO 2.26E-01 Gas 1 98 NO

TXWesternRefini

ng F-4180 CO 2.26E-01 Gas 1 99 NO

TXRohmHaasDe

erPark ACET-2B-5 CO 2.30E-01 Gas 1 100 NO

TXDeerParkRefi

nery H5301 CO 2.40E-01 Gas 1 101 NO

TXDeerParkRefi

nery H5302 CO 2.40E-01 Gas 1 102 NO

TXDeerParkRefi

nery H5303 CO 2.40E-01 Gas 1 103 NO

TXDeerParkRefi

nery H5304 CO 2.40E-01 Gas 1 104 NO

TXDeerParkRefi

nery H5305 CO 2.40E-01 Gas 1 105 NO

TXDeerParkRefi

nery H5350 CO 2.40E-01 Gas 1 106 NO

OKConocoPhillip

sPoncaCity H-8602 CO 2.43E-01 Gas 1 107 NO

TXRohmHaasDe

erPark ACET-2A-4 CO 2.60E-01 Gas 1 108 NO

NJSunocoWestv

ille Boiler #5 CO 2.62E-01 Gas 1 109 NO

PASunocoPhilad

elphia CU-138 CO 2.64E-01 Gas 1 110 NO

TXDiamondSha

mrockMcKee B-3 (Boiler #10) CO 2.64E-01 Gas 1 111 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MSChevronPasc

agoula F-6250 CO 2.66E-01 Gas 1 112 NO

MAUMass EU#7 CO 2.71E-01 Gas 1 113 NO

ORCascadePaci

ficPulp PB2EU CO 2.71E-01 Gas 1 114 NO

KYCatlettsburgR

efining 2-103-B-3 CO 2.71E-01 Gas 1 115 NO

WVQuadGraphis

Martinsburg B-03 CO 2.71E-01 Gas 1 116 NO

TXWesternRefini

ng B-1 CO 2.72E-01 Gas 1 117 NO

TXWesternRefini

ng B-3 CO 2.84E-01 Gas 1 118 NO

LAWestlakeStyr

ene 2-90 CO 2.88E-01 Gas 1 119 NO

TXL3Communication

sIntergrated A0769 CO 3.00E-01 Gas 1 120 NO

KYCatlettsburgR

efining 2-103-B-2 CO 3.02E-01 Gas 1 121 NO

LAShellChemica

Geismar Boiler F-U202 CO 3.10E-01 Gas 1 122 NO

TXEquistarChem

icals QE5802UB CO 3.40E-01 Gas 1 123 NO

TXRohmHaasDe

erPark ACET-2B-3 CO 3.47E-01 Gas 1 124 NO

TXDiamondSha

mrockMcKee

H-9 (#2 Crude 

Charge - 

Petrochem) CO 3.47E-01 Gas 1 125 NO

WYSinclairCasp

er

Pt. 26 #2 

Reformer Heater CO 3.50E-01 Gas 1 126 NO

MSChevronPasc

agoula F-8130 CO 3.64E-01 Gas 1 127 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXValeroTexasC

ity Heater 13-1421 CO 3.67E-01 Gas 1 128 NO

TXWesternRefini

ng F-3902 CO 3.73E-01 Gas 1 129 NO

MTCHSLaurel14

01 H-902 CO 3.77E-01 Gas 1 130 NO

TXValeroCorpus

Christi 148-H-1 CO 4.00E-01 Gas 1 131 NO

TXValeroCorpus

Christi 148-H-2 CO 4.00E-01 Gas 1 132 NO

ILRentech S-7 CO 4.06E-01 Gas 1 133 NO

TXDiamondSha

mrockMcKee

H-36 (#2 NAP 

Hydrotreater 

Charge) CO 4.29E-01 Gas 1 134 NO

NJSunocoWestv

ille Boiler #7 CO 4.38E-01 Gas 1 135 NO

MSChevronPasc

agoula F-6531 CO 4.46E-01 Gas 1 136 NO

LAAmericasStyr

enics HS-1102 CO 4.57E-01 Gas 1 137 NO

FLSolutiaIncPen

sacola B-7 CO 4.73E-01 Gas 1 138 NO

TNValeroMemph

is

P044-DHT 18 

Stripper Reboiler 

Heater CO 4.74E-01 Gas 1 139 NO

OKConocoPhillip

sPoncaCity H-9901 CO 4.90E-01 Gas 1 140 NO

OHUSEnrichme

ntCorpPiketon

X-6002 Boiler 

No. 1 (North) CO 4.96E-01 Gas 1 141 NO

OKQuadGraphic

sOKCity SG03 CO 4.96E-01 Gas 1 142 NO

CATesoro

S-922 Furnace 

22 CO 5.00E-01 Gas 1 143 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXInvistaVictoria 16STK001 CO 5.15E-01 Gas 1 144 NO

TXWesternRefini

ng F-1010 CO 5.19E-01 Gas 1 145 NO

TXRohmHaasDe

erPark N-14 CO 5.23E-01 Gas 1 146 NO

TXValeroTexasC

ity Heater 13-1401 CO 5.33E-01 Gas 1 147 NO

OKSinclairTulsa

Refining

NHDS Charge 

Heater CO 5.41E-01 Gas 1 148 NO

LACalumet

VII-L Hydrogen 

plant heater 

2006 R-101-A CO 5.41E-01 Gas 1 149 NO

NJMerckRahway

E750009 - Boiler 

#9 CO 5.41E-01 Gas 1 150 NO

TXOccidentalCh

emGregory

VCM Plant 2 

Furnace 1 CO 5.50E-01 Gas 1 151 NO

TXOccidentalCh

emGregory

VCM Plant 2 

Furnace 2 CO 5.50E-01 Gas 1 152 NO

CATesoro

S-974 Furance 

55 CO 5.56E-01 Gas 1 153 NO

MSChevronPasc

agoula F-2410 CO 5.56E-01 Gas 1 154 NO

TXValeroCorpus

Christi 116-H-125B CO 5.67E-01 Gas 1 155 NO

TXValeroCorpus

Christi 116-H-125C CO 5.67E-01 Gas 1 156 NO

TXValeroCorpus

Christi 116-H-125A CO 5.67E-01 Gas 1 157 NO

KYCatlettsburgR

efining 2-104-B-1 CO 5.83E-01 Gas 1 158 NO

MSChevronPasc

agoula F-2930 CO 5.86E-01 Gas 1 159 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILJohnDeereHar

vester B10 CO 5.86E-01 Gas 1 160 NO

CATesoro

S-908 Furnace 8 

/ S-1470 

Furnace 71 CO 6.00E-01 Gas 1 161 NO

CATesoro

S-937 Furnace 

37 CO 6.00E-01 Gas 1 162 NO

KSSpiritAero 3-224R-BLR4 CO 6.00E-01 Gas 1 163 NO

MTCHSLaurel14

01

NHT Charge 

Heater CO 6.00E-01 Gas 1 164 NO

PADominionHarr

ison Heater 1 CO 6.00E-01 Gas 1 165 NO

NCCampLejeune

MCB C-AS-4151-16 CO 6.01E-01 Gas 1 166 NO

ILWoodRiverRefi

nery HTR-ULD-H4 CO 6.17E-01 Gas 1 167 NO

MABostonGener

atingMysticStatio

n EU-17 CO 6.63E-01 Gas 1 168 NO

TXValeroTexasC

ity Heater 50 CO 6.67E-01 Gas 1 169 NO

TXValeroCorpus

Christi 139-H-7 CO 6.95E-01 Gas 1 170 NO

PASunocoPhilad

elphia CU-137 CO 6.95E-01 Gas 1 171 NO

CATesoro

S-927 Furnace 

27 CO 7.00E-01 Gas 1 172 NO

CAMillerCoorsIr

windale D2 Keeler CO 7.00E-01 Gas 1 173 NO

WYShuteCreek2

926 1H-9201 CO 7.22E-01 Gas 1 174 NO

MSGAGulfAberd

een Boiler 4 CO 7.33E-01 Gas 1 175 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WVMountainStat

eCarbonFollansb

ee S1 CO 7.33E-01 Gas 1 176 NO

MSChevronPasc

agoula F-6102 CO 7.62E-01 Gas 1 177 NO

MSChevronPasc

agoula F-6101 CO 7.62E-01 Gas 1 178 NO

WATransAltaCe

ntralia

EU 12 BHP 

Auxiliary Boiler CO 7.63E-01 Gas 1 179 NO

TNValeroMemph

is

P003 - West 

Crude Unit 

Heater CO 7.67E-01 Gas 1 180 NO

TXOxyVinylsPas

adena F6 Boiler CO 7.67E-01 Gas 1 181 NO

KSCoffeyvilleRef

inery IA-06-FH0035 CO 7.67E-01 Gas 1 182 NO

OKConocoPhillip

sPoncaCity H-1001 CO 7.90E-01 Gas 1 183 NO

MSChevronPasc

agoula F-6550 CO 8.20E-01 Gas 1 184 NO

MSChevronPasc

agoula F-6560 CO 8.20E-01 Gas 1 185 NO

MSChevronPasc

agoula F-6570 CO 8.20E-01 Gas 1 186 NO

MSChevronPasc

agoula F-6580 CO 8.20E-01 Gas 1 187 NO

UTHollyRefining 19H1 CO 8.53E-01 Gas 1 188 NO

MSChevronPasc

agoula F-1101 CO 8.85E-01 Gas 1 189 NO

MSChevronPasc

agoula F-1102 CO 8.85E-01 Gas 1 190 NO

KYCatlettsburgR

efining 2-103-B-1 CO 9.01E-01 Gas 1 191 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXDiamondSha

mrockThreeRive

rs H-28002 CO 9.02E-01 Gas 1 192 NO

WYSinclairWyo

ming

Pt 60 #4HDS 

Heater HT-101 CO 9.02E-01 Gas 1 193 NO

NJMerckRahway

E750005 - Boiler 

#5 CO 9.02E-01 Gas 1 194 NO

ILMarathon 16F-3A CO 9.47E-01 Gas 1 195 NO

ILMarathon 16F-3B CO 9.47E-01 Gas 1 196 NO

ILMarathon 16F-3C CO 9.47E-01 Gas 1 197 NO

ILMarathon 16F-3D CO 9.47E-01 Gas 1 198 NO

WVWeyerhaeus

erBuckhannon 001-02 CO 9.67E-01 Gas 1 199 NO

CAAerojet Small Boilers CO 1.00E+00 Gas 1 200 NO

CATesoro S-909 Furnace 9 CO 1.00E+00 Gas 1 201 NO

CATesoro

S-912 Furnace 

12 CO 1.00E+00 Gas 1 202 NO

CATesoro

S-913 Furnace 

13 CO 1.00E+00 Gas 1 203 NO

CATesoro

S-916 Furnace 

16 CO 1.00E+00 Gas 1 204 NO

CATesoro

S-928 Furnace 

28 CO 1.00E+00 Gas 1 205 NO

CATesoro

S-929 Furnace 

29 CO 1.00E+00 Gas 1 206 NO

CATesoro

S-930 Furnace 

30 CO 1.00E+00 Gas 1 207 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

CATesoro

S-932 Furance 

32 CO 1.00E+00 Gas 1 208 NO

CATesoro

S-933 Furnace 

33 CO 1.00E+00 Gas 1 209 NO

CATesoro

S-934 Furnace 

34 CO 1.00E+00 Gas 1 210 NO

TXLyondellChan

nelview F66850 CO 1.00E+00 Gas 1 211 NO

TXLyondellChan

nelview F67830 CO 1.00E+00 Gas 1 212 NO

KYCatlettsburgR

efining 2-26-B-2 CO 1.01E+00 Gas 1 213 NO

DEDuPontEdge

moor OX-5 CO 1.03E+00 Gas 1 214 NO

MTCHSLaurel14

01

H-201 Reactor 

Charge Heater CO 1.03E+00 Gas 1 215 NO

ILMarathon 69F-1A CO 1.04E+00 Gas 1 216 NO

TXValeroCorpus

Christi 108-H-3 CO 1.04E+00 Gas 1 217 NO

MNBoisePaper1

212 EU 440 Boiler #3 CO 1.05E+00 Gas 1 218 NO

ILMarathon 74F-1 CO 1.07E+00 Gas 1 219 NO

TXDiamondSha

mrockMcKee

H-48 (Diesel 

HDS Charge) CO 1.08E+00 Gas 1 220 NO

TXValeroCorpus

Christi 108-H-5 CO 1.08E+00 Gas 1 221 NO

WABoeingRento

n BOIL04 CO 1.08E+00 Gas 1 222 NO

ALBoiseWhitePa

perJackson 102-0001-X020 CO 1.08E+00 Gas 1 223 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

CATesoro

S-950 Furnace 

50 CO 1.10E+00 Gas 1 224 NO

PADominionSabi

nsville Kewanee Boiler CO 1.10E+00 Gas 1 225 NO

TXDeerParkRefi

nery H5404 CO 1.14E+00 Gas 1 226 NO

TXValeroCorpus

Christi 112-H-1 CO 1.15E+00 Gas 1 227 NO

CATesoro

S-971 Furnace 

53 CO 1.17E+00 Gas 1 228 NO

COSEIncComm

erceCity H-1716 CO 1.19E+00 Gas 1 229 NO

OHLimaRefining

Company B028 CO 1.20E+00 Gas 1 230 NO

OKVRCOklahom

a H-6701 CO 1.21E+00 Gas 1 231 NO

TXDeerParkRefi

nery H613 CO 1.22E+00 Gas 1 232 NO

TXDiamondSha

mrockMcKee

H-64 (#4 

Hydrotreater 

Charge) CO 1.22E+00 Gas 1 233 NO

ILCognisCorp Boiler #1 CO 1.23E+00 Gas 1 234 NO

MSChevronPasc

agoula F-5337A CO 1.24E+00 Gas 1 235 NO

KYCatlettsburgR

efining 2-23-B-6 CO 1.24E+00 Gas 1 236 NO

NJConocoPhillip

sBayway F-500 CO 1.25E+00 Gas 1 237 NO

MTMontanaRefi

ning

H-1701 HTU 

Heater CO 1.27E+00 Gas 1 238 NO

MSGeorgiaPacifi

cMonticello

AA-404 (UT-4) 

Power Boiler CO 1.27E+00 Gas 1 239 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MNVersoPaper EU015 Wickes CO 1.29E+00 Gas 1 240 NO

MTCHSLaurel14

01

H-101 Reformer 

Heater CO 1.29E+00 Gas 1 241 NO

TXL3Communication

sIntergrated E2011 CO 1.30E+00 Gas 1 242 NO

KYCatlettsburgR

efining 1-2-B-3 CO 1.30E+00 Gas 1 243 NO

FLSolutiaIncPen

sacola H2 Plant CO 1.35E+00 Gas 1 244 NO

IAADMClinton

EUCOG-4 #1 

Gas Fired Boiler CO 1.35E+00 Gas 1 245 NO

LAValeroRefinin

g F-15-05 CO 1.35E+00 Gas 1 246 NO

LAValeroRefinin

g F-53-1A CO 1.35E+00 Gas 1 247 NO

LAValeroRefinin

g F-53-1B CO 1.35E+00 Gas 1 248 NO

LAValeroRefinin

g F-53-1C CO 1.35E+00 Gas 1 249 NO

LAValeroRefinin

g F-53-1D CO 1.35E+00 Gas 1 250 NO

LAValeroRefinin

g F-72-703 CO 1.35E+00 Gas 1 251 NO

LAValeroRefinin

g GDU Heater CO 1.35E+00 Gas 1 252 NO

LAValeroRefinin

g H-60-1 CO 1.35E+00 Gas 1 253 NO

LAValeroRefinin

g H-60-2 CO 1.35E+00 Gas 1 254 NO

LAValeroRefinin

g H-60-3 CO 1.35E+00 Gas 1 255 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

LAValeroRefinin

g H-60-4 CO 1.35E+00 Gas 1 256 NO

LAValeroRefinin

g

KHT Heater F-33-

05 CO 1.35E+00 Gas 1 257 NO

LAValeroRefinin

g

NHT Reactor 

Feed Heater H39-01 CO 1.35E+00 Gas 1 258 NO

LAValeroRefinin

g

NHT Stripper 

Feed Heater H39-02 CO 1.35E+00 Gas 1 259 NO

LAValeroRefinin

g

NHT Stripper 

Reboiler H-39-03 CO 1.35E+00 Gas 1 260 NO

LAValeroRefinin

g

SMR1 Heater 

No. 1 CO 1.35E+00 Gas 1 261 NO

LAValeroRefinin

g

SMR1 Heater 

No. 2 CO 1.35E+00 Gas 1 262 NO

OKTerraNitrogen

#2 Primary 

Reformer CO 1.35E+00 Gas 1 263 NO

TXBASFFreepor

t

Dehydro Heaters2 CO 1.35E+00 Gas 1 264 NO

TXBASFFreepor

t Vaporizers CO 1.35E+00 Gas 1 265 NO

TXBASFFreepor

t W-900A CO 1.35E+00 Gas 1 266 NO

TXLubrizolBaypo

rt BOIL-2 CO 1.35E+00 Gas 1 267 NO

TXSolutiaInc 51H5 CO 1.35E+00 Gas 1 268 NO

TXTotalPetroche

mPortArthur 51DHT1H-3 CO 1.35E+00 Gas 1 269 NO

TXTotalPetroche

mPortArthur 52DHT2H-1 CO 1.35E+00 Gas 1 270 NO

WAGraysHarbor

Paper

No. 9 Boiler 

(EU3) CO 1.35E+00 Gas 1 271 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WYSinclairWyo

ming

Pt 10 781 

Naphtha Splitter 

Heater CO 1.35E+00 Gas 1 272 NO

DEPremcorGrou

pValero 21-H-701 CO 1.35E+00 Gas 1 273 NO

VAUniversityofVi

rginia 7103-1-04R CO 1.37E+00 Gas 1 274 NO

NJHessCorpPortReading U19 - H2 Heater CO 1.40E+00 Gas 1 275 NO

CATesoro

S-904 No. 6 

Boiler CO 1.40E+00 Gas 1 276 NO

OHLimaRefining

Company B004 CO 1.40E+00 Gas 1 277 NO

NYFarRockaway

PowerStation U-HB002 CO 1.42E+00 Gas 1 278 NO

IAMidAmericanE

nergyBettendorf

390 H1 CO 1.42E+00 Gas 1 279 NO

LALakeCharlesC

hemical

LAB-LH-3 (Hot 

Oil Heater) CO 1.43E+00 Gas 1 280 NO

TXDowChemical

Freeport2629 B27P3S511 CO 1.43E+00 Gas 1 281 NO

ILMarathon 74F-2 CO 1.44E+00 Gas 1 282 NO

MSChevronPasc

agoula F-8620 CO 1.44E+00 Gas 1 283 NO

TXDowChemical

LaPorte B2105 CO 1.47E+00 Gas 1 284 NO

NJMerckRahway

E750003 - Boiler 

#3 CO 1.49E+00 Gas 1 285 NO

OHFordClevelan

dCasting

Boiler No. 4 

(BO23) CO 1.49E+00 Gas 1 286 NO

CATesoro

S-972 Furnace 

54 CO 1.50E+00 Gas 1 287 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXRohmHaasDe

erPark ACET-2A-5 CO 1.53E+00 Gas 1 288 NO

WATesoroAnaco

rtes F-104 CO 1.53E+00 Gas 1 289 NO

TXOxyVinylsPas

adena F7 Boiler CO 1.56E+00 Gas 1 290 NO

TNValeroMemph

is

P043 - DHT 18 

Reactor Feed 

Heater CO 1.58E+00 Gas 1 291 NO

WVMountainStat

eCarbonFollansb

ee S5 CO 1.58E+00 Gas 1 292 NO

MTCHSLaurel14

01 H-901 CO 1.59E+00 Gas 1 293 NO

TXDowChemical

Freeport2629 B56P9FB1 CO 1.60E+00 Gas 1 294 NO

TXDowChemical

Freeport2629 B56P9FB2 CO 1.60E+00 Gas 1 295 NO

TXDowChemical

Freeport2629 B56P9FB3 CO 1.60E+00 Gas 1 296 NO

TXDowChemical

Freeport2629 B56P9FB4 CO 1.60E+00 Gas 1 297 NO

TXValeroTexasC

ity Boiler 27 CO 1.60E+00 Gas 1 298 NO

OHDukeEnergy

GenerationCinci

nnati B045 (PB2) CO 1.62E+00 Gas 1 299 NO

NJMerckRahway

E750011 - Boiler 

#11 CO 1.62E+00 Gas 1 300 NO

OKSinclairTulsa

Refining

Pt. 19 Scanfiner 

Charge Heater CO 1.62E+00 Gas 1 301 NO

MTExxonMobilBi

llings F-1201 CO 1.63E+00 Gas 1 302 NO

TXRohmHaasDe

erPark N-3 CO 1.65E+00 Gas 1 303 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXDeerParkRefi

nery H31001 CO 1.65E+00 Gas 1 304 NO

TXDeerParkRefi

nery H31002 CO 1.65E+00 Gas 1 305 NO

OHLimaRefining

Company B029 CO 1.67E+00 Gas 1 306 NO

WIMurphyOilRefi

nery GGU 29-H01 CO 1.67E+00 Gas 1 307 NO

TXDowChemical

Freeport2629 A36MDH621 CO 1.70E+00 Gas 1 308 NO

VAUniversityofVi

rginia 7103-1-03R CO 1.70E+00 Gas 1 309 NO

MNMinnesotaSo

ybeanProcessor

s Boiler 1 EU026 CO 1.73E+00 Gas 1 310 NO

MNMinnesotaSo

ybeanProcessor

s Boiler 2 EU027 CO 1.73E+00 Gas 1 311 NO

VADuPontSprua

nce

Dowtherm 

Vaporizer No. 3 CO 1.80E+00 Gas 1 312 NO

CAConocoPhillip

sSanFran S# 336 CO 1.80E+00 Gas 1 313 NO

ILMarathon 3F-1 CO 1.80E+00 Gas 1 314 NO

ILMarathon 3F-2 CO 1.80E+00 Gas 1 315 NO

TXDiamondSha

mrockMcKee

H-46 (#1 

Reformer #1 

Interheater) CO 1.80E+00 Gas 1 316 NO

MOMcDonnelDo

uglasStLouis 63-3 CO 1.82E+00 Gas 1 317 NO

TNValeroMemph

is

P021 - No. 10 

Boiler CO 1.85E+00 Gas 1 318 NO

MDUofMaryland EU 001-8 CO 1.90E+00 Gas 1 319 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

LACalumet

VII-g DHT 92-H101 reboiler 

heater CO 1.90E+00 Gas 1 320 NO

COSEIncComm

erceCity H-1717 CO 1.95E+00 Gas 1 321 NO

CAConocoPhillip

sSanFran S# 5 CO 1.97E+00 Gas 1 322 NO

CAConocoPhillip

sSanFran S# 4 CO 1.99E+00 Gas 1 323 NO

CAConocoPhillip

sSanFran S# 11 CO 2.00E+00 Gas 1 324 NO

TXValeroTexasC

ity Heater 34 CO 2.00E+00 Gas 1 325 NO

CAConocoPhillip

sSanFran S# 337 CO 2.05E+00 Gas 1 326 NO

LACitgoLakeCha

rles EQT237 CO 2.05E+00 Gas 1 327 NO

OKONEOKMedf

ord H-4 CO 2.11E+00 Gas 1 328 NO

OKVRCOklahom

a H-404 CO 2.15E+00 Gas 1 329 NO

OKVRCOklahom

a H-405 CO 2.15E+00 Gas 1 330 NO

CAConocoPhillip

sSanFran S# 12 CO 2.17E+00 Gas 1 331 NO

TXBPAmocoTex

asCity MX2-H101 CO 2.17E+00 Gas 1 332 NO

CAConocoPhillip

sSanFran S# 29 CO 2.18E+00 Gas 1 333 NO

TXInternationalP

aperQueenCity PB01 CO 2.20E+00 Gas 1 334 NO

KSCoffeyvilleRef

inery IA-05-FH0036 CO 2.21E+00 Gas 1 335 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

LAPPGLakeCha

rles

Power/UtilitiesPowerhouse CCogeneration 

Unit #2 CO 2.22E+00 Gas 1 336 NO

OKONEOKMedf

ord H-3 CO 2.25E+00 Gas 1 337 NO

MNStPaulParkR

ef EU 087 CO 2.27E+00 Gas 1 338 NO

CAConocoPhillip

sSanFran S# 9 CO 2.27E+00 Gas 1 339 NO

TXTexasPetroch

emicals Boiler No. 9 CO 2.28E+00 Gas 1 340 NO

MSChevronPasc

agoula F-5337B CO 2.30E+00 Gas 1 341 NO

NEAgProcessing

SOY EP 137 CO 2.37E+00 Gas 1 342 NO

LACitgoLakeCha

rles EQT238 CO 2.37E+00 Gas 1 343 NO

CAConocoPhillip

sSanFran S# 3 CO 2.38E+00 Gas 1 344 NO

MDUofMaryland EU 001-2 CO 2.40E+00 Gas 1 345 NO

CATesoro

S-926 Furnace 

26 CO 2.40E+00 Gas 1 346 NO

PADominionFinn

efrock Boiler 3 (039) CO 2.40E+00 Gas 1 347 NO

CAConocoPhillip

sSanFran S# 7 CO 2.40E+00 Gas 1 348 NO

TNValeroMemph

is

P010A - No. 1 

East Crude Unit 

Heater CO 2.44E+00 Gas 1 349 NO

MDUofMaryland EU 001-4 CO 2.45E+00 Gas 1 350 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

CAConocoPhillip

sSanFran S# 36 CO 2.46E+00 Gas 1 351 NO

OKONEOKMedf

ord H-1 CO 2.47E+00 Gas 1 352 NO

TXEquistarChan

nelview F4360C CO 2.48E+00 Gas 1 353 NO

CATesoro

S-1106 Furnace 

72 CO 2.50E+00 Gas 1 354 NO

IAKochNitrogen

Reformer-Aux 

Boiler CO 2.52E+00 Gas 1 355 NO

SCPPGSpartanb

urg

LLR06251 

(Hurst) CO 2.57E+00 Gas 1 356 NO

ALHuntRefining B-06 CO 2.58E+00 Gas 1 357 NO

COSEIncComm

erceCity H-33 CO 2.59E+00 Gas 1 358 NO

TXDowChemical

Freeport2629 B68ALS3 CO 2.62E+00 Gas 1 359 NO

CAConocoPhillip

sSanFran S# 2 CO 2.68E+00 Gas 1 360 NO

LAValeroRefinin

g F-52-01B CO 2.71E+00 Gas 1 361 NO

TXDiamondSha

mrockMcKee

H-8 (HCU 

Fractionation) CO 2.71E+00 Gas 1 362 NO

CAConocoPhillip

sSanFran S# 461 CO 2.71E+00 Gas 1 363 NO

MTCHSLaurel14

01 #11 Boiler CO 2.71E+00 Gas 1 364 NO

MTCHSLaurel14

01 H-1001 CO 2.74E+00 Gas 1 365 NO

GAOFSFitel HWG1 CO 2.75E+00 Gas 1 366 NO

OHSolvayAdvan

cedPolymers B011 CO 2.75E+00 Gas 1 367 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ORBoiseBuilding B1 CO 2.76E+00 Gas 1 368 NO

CAExxonMobilTorrance 75F-1 CO 2.78E+00 Gas 1 369 NO

TXSolutiaInc 50H3 CO 2.80E+00 Gas 1 370 NO

WYSinclairWyo

ming

Pt 74 #2 H2 

Plant Heater CO 2.81E+00 Gas 1 371 NO

TXOccidentalCh

emGregory

CTG Duct 

Burner 2 CO 2.84E+00 Gas 1 372 NO

TXTotalPetroche

mPortArthur 52DHT2H-2 CO 2.89E+00 Gas 1 373 NO

SCEastmanColo

mbia

HTM Heater #3 

(Equip ID 1101) CO 2.92E+00 Gas 1 374 NO

TNValeroMemph

is

P021 - No. 9 

Boiler CO 2.93E+00 Gas 1 375 NO

KYCentralMotor

Wheel Alum. Div. Boiler CO 2.94E+00 Gas 1 376 NO

LADowChemical

Vinyl F-110 CO 2.97E+00 Gas 1 377 NO

PADominionEllis

burg

Boiler 2 (Aux 

Boiler) CO 3.00E+00 Gas 1 378 NO

CAConocoPhillip

sSanFran S# 30 CO 3.06E+00 Gas 1 379 NO

PASunocoMarcu

sHook

040 (10-4 Feed 

Heater) CO 3.09E+00 Gas 1 380 NO

MDNewPageLuke No. 26 CO 3.09E+00 Gas 1 381 NO

TXRohmHaasDe

erPark ACET-2B-2 CO 3.10E+00 Gas 1 382 NO

MTCHSLaurel14

01

FCC Feed 

Preheater CO 3.10E+00 Gas 1 383 NO

NJMerckRahway

E750010 - Boiler 

#10 CO 3.11E+00 Gas 1 384 NO

TXLyondellChan

nelview F96890 CO 3.16E+00 Gas 1 385 NO

OHUSEnrichme

ntCorpPiketon

X-6002 Boiler 

No. 2 (South) CO 3.16E+00 Gas 1 386 NO

FLGPPalatka EU15 CO 3.16E+00 Gas 1 387 NO

ILMarathon 87F-103 CO 3.16E+00 Gas 1 388 NO

GAOFSFitel HWG3 CO 3.20E+00 Gas 1 389 NO

TXValeroTexasC

ity Boiler 18 CO 3.23E+00 Gas 1 390 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXOccidentalCh

emGregory

CTG Duct 

Burner 1 CO 3.25E+00 Gas 1 391 NO

TXTotalPetroche

mPortArthur 50TDPH-1 CO 3.32E+00 Gas 1 392 NO

LAWestlakeVinyl

s

74-07 EDC 

Cracking 

Furnace CO 3.38E+00 Gas 1 393 NO

MSChevronPasc

agoula F-5380B CO 3.51E+00 Gas 1 394 NO

IACargillIowaFall

s EP 40 CO 3.53E+00 Gas 1 395 NO

OKONEOKMedf

ord H-6 CO 3.54E+00 Gas 1 396 NO

TXGoodyearTyle

r 6-BOIL-3 CO 3.61E+00 Gas 1 397 NO

NJMerckRahway

E750012 - Boiler 

#12 CO 3.70E+00 Gas 1 398 NO

IAMidAmericanE

nergyBettendorf

390 H2 CO 3.74E+00 Gas 1 399 NO

CAProctorGambl

e158 5009 CO 3.74E+00 Gas 1 400 NO

ALHuntRefining AX CO 3.83E+00 Gas 1 401 NO

WVMorgantown

EnergyAssociate

s

S009L (Aux. 

Boiler 1) CO 4.00E+00 Gas 1 402 NO

LAValeroRefinin

g CCR Heater CO 4.06E+00 Gas 1 403 NO

FLIPPensacola

Power Boiler 5 / 

EU ID 02 CO 4.06E+00 Gas 1 404 NO

AKBPExploratio

nCGF

NGI-19-1402 

(EU ID 13) CO 4.06E+00 Gas 1 405 NO

PADominionGre

enlick Boiler 2 CO 4.10E+00 Gas 1 406 NO

MSChevronPasc

agoula F-8300A CO 4.15E+00 Gas 1 407 NO

TXTexasPetroch

emicals Boiler No. 10 CO 4.22E+00 Gas 1 408 NO

TXValeroCorpus

Christi 129-H-301 CO 4.24E+00 Gas 1 409 NO

MSChevronPasc

agoula F-1601 CO 4.26E+00 Gas 1 410 NO

TXDiamondSha

mrockThreeRive

rs H-047 CO 4.27E+00 Gas 1 411 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

LAPCSNitrogen

Primary 

Reformer CO 4.42E+00 Gas 1 412 NO

TXDiamondSha

mrockMcKee B-4 (Boiler #11) CO 4.44E+00 Gas 1 413 NO

CANUMMI S1056 CO 4.47E+00 Gas 1 414 NO

OKQuadGraphic

sOKCity SG01 CO 4.51E+00 Gas 1 415 NO

TXValeroCorpus

Christi 139-H-3A CO 4.76E+00 Gas 1 416 NO

TXTexasPetroch

emicals Boiler No. 11 CO 4.79E+00 Gas 1 417 NO

LACalumet

II-SA #1 

Platformer 

charge heater CO 4.80E+00 Gas 1 418 NO

IAUofIowa

EP44 Temp 

Boiler 2 CO 4.84E+00 Gas 1 419 NO

ORCascadePaci

ficPulp PB1EU CO 4.87E+00 Gas 1 420 NO

OHHondaMAP

Boiler House 

Boiler 5 CO 4.96E+00 Gas 1 421 NO

TXTotalPetroche

mPortArthur 51DHT1H-1 CO 4.96E+00 Gas 1 422 NO

INNucorSteel VTD Boiler CO 5.00E+00 Gas 1 423 NO

OKConocoPhillip

sPoncaCity H-6007 CO 5.25E+00 Gas 1 424 NO

NJDSMNutrition

al Boiler 3 CO 5.32E+00 Gas 1 425 NO

DEPremcorGrou

pValero 29-H-4 CO 5.41E+00 Gas 1 426 NO

MAMirantCanal Aux Boiler A CO 5.41E+00 Gas 1 427 NO

LAShellChemica

Geismar Boiler F-U205 CO 5.42E+00 Gas 1 428 NO

OKConocoPhillip

sPoncaCity H-6014 CO 5.46E+00 Gas 1 429 NO

CAProctorGambl

e158 5006 CO 5.50E+00 Gas 1 430 NO

ILJLMChemicals

BlueIsland Boiler 1 CO 5.50E+00 Gas 1 431 NO

MSChevronPasc

agoula F-8510 CO 5.51E+00 Gas 1 432 NO

PADominionFinn

efrock Boiler 2 CO 5.55E+00 Gas 1 433 NO

PABellefieldPlan

t Boiler 7 CO 5.86E+00 Gas 1 434 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXValeroTexasC

ity Heater 27 CO 5.93E+00 Gas 1 435 NO

TXDowChemical

Freeport2629 A32CSH301 CO 6.00E+00 Gas 1 436 NO

WIMurphyOilRefi

nery GGU 29-H02 CO 6.30E+00 Gas 1 437 NO

TXDowChemical

LaPorte B2104 CO 6.33E+00 Gas 1 438 NO

CANUMMI S1057 CO 6.60E+00 Gas 1 439 NO

IDTASCONamp

a Riley Boiler CO 6.60E+00 Gas 1 440 NO

OKSinclairTulsa

Refining

NHDS Stripper 

Reboiler CO 6.68E+00 Gas 1 441 NO

LAPPGLakeCha

rles

Power/UtilitiesPowerhouse CCogeneration 

Unit #1 CO 6.76E+00 Gas 1 442 NO

COCheyennePla

insCompStation H-8702 CO 6.77E+00 Gas 1 443 NO

CAProctorGambl

e158 5005 CO 6.77E+00 Gas 1 444 NO

PAUnitedRefinin

gWarrant 56 CO 6.87E+00 Gas 1 445 NO

WYBurlingtonRe

sources B-4301-3 CO 7.02E+00 Gas 1 446 NO

GARobinsAFB B016 CO 7.03E+00 Gas 1 447 NO

LABoiseNewspri

ntDeRidder 86-02 CO 7.12E+00 Gas 1 448 NO

LADeltech HB-513 CO 7.42E+00 Gas 1 449 NO

OKWynnewood H48001 CO 7.43E+00 Gas 1 450 NO

TXSolutiaInc 50H1-3 CO 7.43E+00 Gas 1 451 NO

OHSolaeBellvue B010 CO 7.47E+00 Gas 1 452 NO

WYOCIWyomin

g Boiler 3 CO 7.67E+00 Gas 1 453 NO

MTCHSLaurel14

01

H-202 

Fractiontor Feed 

Heater CO 7.69E+00 Gas 1 454 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXValeroTexasC

ity Heater 13-1480 CO 8.07E+00 Gas 1 455 NO

LAValeroRefinin

g 401E Boiler CO 8.12E+00 Gas 1 456 NO

TXHuntsmanPet

rochemical H-A-1 CO 8.12E+00 Gas 1 457 NO

DEPremcorGrou

pValero 29-H-8 CO 8.12E+00 Gas 1 458 NO

NJPassaicValley

Sewerage U20-B2 CO 8.19E+00 Gas 1 459 NO

NCCargillFayette

ville ES-41 CO 8.21E+00 Gas 1 460 NO

PASunocoMarcu

sHook

706 (12-4 LSG 

Stabilizer 

Heater, H02) CO 8.22E+00 Gas 1 461 NO

TXDeerParkRefi

nery H5500 CO 8.30E+00 Gas 1 462 NO

WVQuadGraphis

Martinsburg B-04 CO 8.39E+00 Gas 1 463 NO

NJPassaicValley

Sewerage U20-B1 CO 8.41E+00 Gas 1 464 NO

TXDowChemical

Freeport2629 B27P3S521 CO 8.43E+00 Gas 1 465 NO

UTBigWestOil H-404 CO 8.57E+00 Gas 1 466 NO

WYRawlinsNGL H-1 CO 8.57E+00 Gas 1 467 NO

LAValeroRefinin

g 401D Boiler CO 8.57E+00 Gas 1 468 NO

IDTASCONamp

a

Babcock and 

Wilcox (B&W) 

#1 CO 8.66E+00 Gas 1 469 NO

IDTASCONamp

a

Babcock and 

Wilcox (B&W) 

#2 CO 8.66E+00 Gas 1 470 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MSChevronPasc

agoula F-8110 CO 8.66E+00 Gas 1 471 NO

OHPPGCirclevill

e B014 CO 8.68E+00 Gas 1 472 NO

PADominionHarr

ison Boiler 2 CO 8.70E+00 Gas 1 473 NO

PASunocoPhilad

elphia CU-009 CO 8.80E+00 Gas 1 474 NO

TXBASFFreepor

t B-20C CO 9.02E+00 Gas 1 475 NO

TXValeroTexasC

ity Heater 31 CO 9.08E+00 Gas 1 476 NO

TXValeroTexasC

ity Heater 32 CO 9.08E+00 Gas 1 477 NO

NJHessCorpPortReading U4 - Boiler #3 CO 9.37E+00 Gas 1 478 NO

LADowChemical

Vinyl F-103 CO 9.43E+00 Gas 1 479 NO

IAADMClintonCo

rn

EU54-1B Boiler 

No. 10 CO 9.47E+00 Gas 1 480 NO

MDSeverstalSpa

rrows 3BLR CO 9.47E+00 Gas 1 481 NO

TXSolutiaInc 51H1 CO 9.63E+00 Gas 1 482 NO

GARobinsAFB B018 CO 9.98E+00 Gas 1 483 NO

GALockheedMar

tin 2580 CO 1.01E+01 Gas 1 484 NO

PADominionHarr

ison Heater 2 CO 1.02E+01 Gas 1 485 NO

TXDiamondSha

mrockMcKee

H-11 (#2 Crude - 

Anderson) CO 1.04E+01 Gas 1 486 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXDeerParkRefi

nery H36100 CO 1.05E+01 Gas 1 487 NO

TXDiamondSha

mrockMcKee

H-2 (#1 Crude 

Vacuum) CO 1.05E+01 Gas 1 488 NO

SCMarlboroPap

er Package Boiler CO 1.06E+01 Gas 1 489 NO

MOAnheuserBus

ch Boiler7 CO 1.07E+01 Gas 1 490 NO

LACalumet

VII-f DHT 92-H100 heater CO 1.08E+01 Gas 1 491 NO

NJHessCorpPortReading U4 - Boiler #4 CO 1.12E+01 Gas 1 492 NO

WYOCIWyomin

g Boiler 4 CO 1.13E+01 Gas 1 493 NO

PAYorkJCIGrantley B49 Boilers CO 1.15E+01 Gas 1 494 NO

TXValeroTexasC

ity Heater 29 CO 1.15E+01 Gas 1 495 NO

IAUofIowa

EP43 Temp 

Boiler 1 CO 1.19E+01 Gas 1 496 NO

TXBASFFreepor

t W-500H CO 1.22E+01 Gas 1 497 NO

MTCHSLaurel14

01

Coker Charge 

Heater CO 1.27E+01 Gas 1 498 NO

OHMarathonRefi

neryCanton

B022 - HDT 

Heater CO 1.27E+01 Gas 1 499 NO

ORSierraPineSp

ringfield SPSPBL01 CO 1.29E+01 Gas 1 500 NO

OKONEOKMedf

ord H-7 CO 1.30E+01 Gas 1 501 NO

NJAPIFoils 1 CO 1.35E+01 Gas 1 502 NO

COSEIncComm

erceCity B501 CO 1.35E+01 Gas 1 503 NO

MIMarathonOilD

etroit

14H8 - CCR 

Charge Heater CO 1.35E+01 Gas 1 504 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MIMarathonOilD

etroit

8H1 - GOHT 

Charge Heater CO 1.35E+01 Gas 1 505 NO

DEPremcorGrou

pValero 29-H-5 CO 1.35E+01 Gas 1 506 NO

OKONEOKMedf

ord H-2 CO 1.43E+01 Gas 1 507 NO

ORWeyerhaeus

erCoWarrentonL

umberMill 4-NGB CO 1.43E+01 Gas 1 508 NO

LAWestlakeVinyl

s

03-04 Utility 

Boiler CO 1.44E+01 Gas 1 509 NO

IAMidAmericanE

nergyCouncil 

Bluffs391

Unit 4 Auxilliary 

Boiler CO 1.46E+01 Gas 1 510 NO

WIFlambeauRiv

erPaper B20 CO 1.53E+01 Gas 1 511 NO

MIZeelandFarm Large Boiler CO 1.55E+01 Gas 1 512 NO

WAUSOilandRef

iningTacoma H-202 CO 1.58E+01 Gas 1 513 NO

TXDowChemical

Freeport2629 B27P3S503 CO 1.59E+01 Gas 1 514 NO

PADominionGre

enlick Heater 4 CO 1.60E+01 Gas 1 515 NO

TXBASFFreepor

t Dehydro Heaters CO 1.62E+01 Gas 1 516 NO

TXDiamondSha

mrockMcKee

H-26 (#2 

Vacuum Heater) CO 1.63E+01 Gas 1 517 NO

TXLubrizolCorp

DeerParkPlant BOILER NO.6 CO 1.67E+01 Gas 1 518 NO

TXWesternRefini

ng F-3901 CO 1.75E+01 Gas 1 519 NO

COSEIncComm

erceCity H103 CO 1.76E+01 Gas 1 520 NO

IAADMClintonCo

rn

EU504-2 WWTP 

Oil Heater CO 1.78E+01 Gas 1 521 NO

ILFlintHillsResou

rces CB-706 CO 1.78E+01 Gas 1 522 NO

CATesoro

S-919 Furnace 

19 CO 1.80E+01 Gas 1 523 NO

SCDuPontTeijin

Florence Boiler #1 CO 1.85E+01 Gas 1 524 NO

TXWesternRefini

ng F-1011 CO 1.85E+01 Gas 1 525 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

CASoCalGas H-401B CO 1.93E+01 Gas 1 526 NO

LAAmericasStyr

enics HB-3500 CO 1.96E+01 Gas 1 527 NO

CASoCalGas H-401A CO 1.97E+01 Gas 1 528 NO

SCDuPontTeijin

Florence Boiler #2 CO 1.98E+01 Gas 1 529 NO

TXFirestonePoly

mersLLC E-B110 CO 1.99E+01 Gas 1 530 NO

OHADMFostoria

1778 B005 CO 2.00E+01 Gas 1 531 NO

MAMirantCanal Aux Boiler B CO 2.12E+01 Gas 1 532 NO

TNValeroMemph

is

P013-DHDS 

Reactor Chrg Htr 

& Fractionator 

Reboiler CO 2.15E+01 Gas 1 533 NO

LAConocoPhillip

sUnit891

891-H-1 Delayed 

Coker Charge 

Heater CO 2.20E+01 Gas 1 534 NO

LADowChemical

Vinyl F-106 CO 2.27E+01 Gas 1 535 NO

MIPfizerGlobal1

179 EUBoiler6 CO 2.28E+01 Gas 1 536 NO

OKQuadGraphic

sOKCity SG02 CO 2.30E+01 Gas 1 537 NO

PAINDESPEC 040 CO 2.32E+01 Gas 1 538 NO

PADominionFinn

efrock Boiler (Pennco) CO 2.35E+01 Gas 1 539 NO

TXValeroTexasC

ity Boiler 26 CO 2.37E+01 Gas 1 540 NO

MSWeyerhaeus

erColumbus AA-019 CO 2.48E+01 Gas 1 541 NO

LADowChemical

Vinyl F-101 CO 2.50E+01 Gas 1 542 NO

TXHuntsmanPor

tNeches Boiler HK-11 CO 2.51E+01 Gas 1 543 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXTotalPetroche

mPortArthur 01ACU1H101 CO 2.53E+01 Gas 1 544 NO

PADominionEllis

burg Heater 4 (045) CO 2.53E+01 Gas 1 545 NO

TXDiamondSha

mrockMcKee

H-40 (#1 PDA 

Asplalt Heater) CO 2.53E+01 Gas 1 546 NO

MIPfizerGlobal1

179 EUBoiler2 CO 2.54E+01 Gas 1 547 NO

KSGMFairfax Boiler No.4 CO 2.54E+01 Gas 1 548 NO

MIFordWayneAs

sembly

Powerhouse 

Boiler 3 CO 2.57E+01 Gas 1 549 NO

PASunocoMarcu

sHook D Boiler (FPLE) CO 2.57E+01 Gas 1 550 NO

VADuPontSprua

nce

Dowtherm 

Vaporizer No. 5 CO 2.60E+01 Gas 1 551 NO

LADowChemical

Vinyl F-104 CO 2.64E+01 Gas 1 552 NO

CADucommunA

eroStructures B003705 CO 2.65E+01 Gas 1 553 NO

TXValeroCorpus

Christi 139-H-3B CO 2.66E+01 Gas 1 554 NO

MIMarathonOilD

etroit

11H1 - FCCU 

Charge Heater CO 2.71E+01 Gas 1 555 NO

ORGPToledo

EU13 - Power 

Boiler #1 CO 2.72E+01 Gas 1 556 NO

WAConocoPhilli

psFerndale 22F-1E CO 2.73E+01 Gas 1 557 NO

LADowChemical

Vinyl F-105 CO 2.76E+01 Gas 1 558 NO

LACF Industries

No. 2 Urea 

Boiler B CO 2.80E+01 Gas 1 559 NO

TXDiamondSha

mrockThreeRive

rs H-1402 CO 2.81E+01 Gas 1 560 NO

TXDowChemical

Freeport2629 BSRSRHET2 CO 2.83E+01 Gas 1 561 NO

NJDSMNutrition

al Boiler 2 CO 2.84E+01 Gas 1 562 NO

LADowChemical

Vinyl F-102 CO 2.89E+01 Gas 1 563 NO

TXChevronBayto

wn H-602 CO 2.93E+01 Gas 1 564 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ILAbbottNorthCh

icago Boiler #11 CO 2.93E+01 Gas 1 565 NO

ORFlakeboardAl

bany Boil-1 CO 2.94E+01 Gas 1 566 NO

COCheyennePla

insCompStation H-8701 CO 2.98E+01 Gas 1 567 NO

ORIPSpringfield Power Boiler CO 2.98E+01 Gas 1 568 NO

CTCytecWallingf

ord 150 Furnace CO 2.98E+01 Gas 1 569 NO

GARobinsAFB B017 CO 3.02E+01 Gas 1 570 NO

CATesoro

S-951 Furnace 

51 CO 3.04E+01 Gas 1 571 NO

MNAndersonCor

pBayport Boiler 13 EU622 CO 3.04E+01 Gas 1 572 NO

IAADMClintonCo

rn

EU504-1 WWTP 

Oil Heater CO 3.04E+01 Gas 1 573 NO

MSPYCO AA-001 CO 3.09E+01 Gas 1 574 NO

MNAndersonCor

pBayport Boiler 11 EU620 CO 3.14E+01 Gas 1 575 NO

MNAndersonCor

pBayport Boiler 12 EU621 CO 3.14E+01 Gas 1 576 NO

TXLanxessOrange EQ-3V CO 3.25E+01 Gas 1 577 NO

PADominionEllis

burg Heater 5 (052) CO 3.27E+01 Gas 1 578 NO

VADuPontSprua

nce

Dowtherm 

Vaporizer No. 4 CO 3.33E+01 Gas 1 579 NO

MSChevronPasc

agoula F-8300C CO 3.36E+01 Gas 1 580 NO

VAUniversityofVi

rginia 7103-1-02R CO 3.39E+01 Gas 1 581 NO

LATembecUSA PB No.4 CO 3.41E+01 Gas 1 582 NO

TXChevronBayto

wn H-530 CO 3.44E+01 Gas 1 583 NO

MDDominionCov

ePoint S004-17 CO 3.45E+01 Gas 1 584 NO

MDDominionCov

ePoint S004-25 CO 3.48E+01 Gas 1 585 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NJPassaicValley

Sewerage U20-B3 CO 3.58E+01 Gas 1 586 NO

IDAgriumNuWes

t S-Nb-1 CO 3.60E+01 Gas 1 587 NO

LAValeroRefinin

g 401C Boiler CO 3.61E+01 Gas 1 588 NO

TXLanxessOrange EQ-1V CO 3.65E+01 Gas 1 589 NO

WAGPCamas

No. 5 Power 

Boiler CO 3.65E+01 Gas 1 590 NO

WVQuadGraphis

Martinsburg B-02 CO 3.67E+01 Gas 1 591 NO

VADuPontSprua

nce

Dowtherm 

Vaporizer No. 6 CO 3.70E+01 Gas 1 592 NO

NJDSMNutrition

al Boiler 4 CO 3.74E+01 Gas 1 593 NO

MDDominionCov

ePoint S004-21 CO 3.78E+01 Gas 1 594 NO

PASunocoMarcu

sHook B Boiler (FPLE) CO 3.79E+01 Gas 1 595 NO

NJSunocoWestv

ille Boiler #6 CO 3.85E+01 Gas 1 596 NO

MOMcDonnelDo

uglasStLouis 103-1 CO 3.87E+01 Gas 1 597 NO

PASunocoMarcu

sHook C Boiler (FPLE) CO 4.01E+01 Gas 1 598 NO

OKTerraNitrogen UC Boiler CO 4.06E+01 Gas 1 599 NO

PADominionGre

enlick Heater 2 CO 4.19E+01 Gas 1 600 NO

KSSpiritAero 3-224R-BLR3 CO 4.19E+01 Gas 1 601 NO

PASunocoMarcu

sHook A Boiler (FPLE) CO 4.20E+01 Gas 1 602 NO

TXLubrizolCorp

DeerParkPlant BOILER NO.4 CO 4.24E+01 Gas 1 603 NO

LACF Industries

No. 2 Urea 

Boiler A CO 4.27E+01 Gas 1 604 NO

ILKoppersInc Boiler #4 CO 4.28E+01 Gas 1 605 NO

LAShellChemica

Geismar Boiler F-U201 CO 4.28E+01 Gas 1 606 NO

NYKodakPark #1 boiler B-514 CO 4.30E+01 Gas 1 607 NO

TXHuntsmanPet

rochemical H-F-2 CO 4.33E+01 Gas 1 608 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXHuntsmanPet

rochemical H-F-3 CO 4.33E+01 Gas 1 609 NO

NYKodakPark #1 boiler B-95 CO 4.35E+01 Gas 1 610 NO

COSEIncComm

erceCity B-6 CO 4.38E+01 Gas 1 611 NO

ILAbbottNorthCh

icago Boiler #10 CO 4.45E+01 Gas 1 612 NO

TXValeroTexasC

ity Heater 60 CO 4.46E+01 Gas 1 613 NO

NYKodakPark 2 boiler B-514 CO 4.47E+01 Gas 1 614 NO

IDPotlatchLewist

on 2 Power Boiler CO 4.50E+01 Gas 1 615 NO

MDDominionCov

ePoint S004-19 CO 4.56E+01 Gas 1 616 NO

OHTateLyleDayt

on B004 CO 4.59E+01 Gas 1 617 NO

MDDominionCov

ePoint S004-22 CO 4.60E+01 Gas 1 618 NO

OHFordClevelan

dCasting

Boiler No. 3 

(BO22) CO 4.60E+01 Gas 1 619 NO

LABoiseNewspri

ntDeRidder 86-01 CO 4.62E+01 Gas 1 620 NO

OHTateLyleDayt

on B002 CO 4.74E+01 Gas 1 621 NO

DEPremcorGrou

pValero 29-H-101 CO 4.74E+01 Gas 1 622 NO

MDDominionCov

ePoint S004-20 CO 4.77E+01 Gas 1 623 NO

CAMillerCoorsIr

windale D3 Keeler CO 4.80E+01 Gas 1 624 NO

MDDominionCov

ePoint S004-24 CO 4.81E+01 Gas 1 625 NO

MDDominionCov

ePoint S004-23 CO 4.81E+01 Gas 1 626 NO

OKConocoPhillip

sPoncaCity B-0008 CO 4.82E+01 Gas 1 627 NO

MDDominionCov

ePoint S004-18 CO 4.84E+01 Gas 1 628 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

PADominionGre

enlick Heater B CO 4.90E+01 Gas 1 629 NO

TXRohmHaasDe

erPark HT-9 CO 4.95E+01 Gas 1 630 NO

GARobinsAFB B014 CO 4.96E+01 Gas 1 631 NO

TXDeerParkRefi

nery H5105 CO 5.09E+01 Gas 1 632 NO

TXDeerParkRefi

nery H63000 CO 5.09E+01 Gas 1 633 NO

CATesoro

S-920 Furnace 

20 CO 5.10E+01 Gas 1 634 NO

TXLanxessOrange BOS-31V CO 5.14E+01 Gas 1 635 NO

VAUniversityofVi

rginia 5575-1-03 CO 5.27E+01 Gas 1 636 NO

NJPassaicValley

Sewerage U20-B4 CO 5.28E+01 Gas 1 637 NO

MDDominionCov

ePoint S004-16 CO 5.43E+01 Gas 1 638 NO

NYKodakPark #2 boiler B-95 CO 5.53E+01 Gas 1 639 NO

LACitgoLakeCha

rles EQT028 CO 5.55E+01 Gas 1 640 NO

MOAnheuserBus

ch Boiler 5 CO 5.58E+01 Gas 1 641 NO

PADominionOak

ford Boiler 2 CO 5.59E+01 Gas 1 642 NO

LACalumet

VII-h sour crude 

heater 9*3-H200 CO 5.68E+01 Gas 1 643 NO

WYSinclairCasp

er

Pt. 18 B-201 

CHD Heater CO 6.00E+01 Gas 1 644 NO

PADominionGre

enlick Heater 1 CO 6.00E+01 Gas 1 645 NO

VAUniversityofVi

rginia 7103-1-05 CO 6.00E+01 Gas 1 646 NO

ILWoodRiverRefi

nery HTR-DU1-F301 CO 6.04E+01 Gas 1 647 NO

VAUniversityofVi

rginia 5575-1-02 CO 6.08E+01 Gas 1 648 NO

NYKodakPark #2 boiler B-502 CO 6.10E+01 Gas 1 649 NO

PADominionGre

enlick Boiler 1 CO 6.20E+01 Gas 1 650 NO

NEAgProcessing

SOY EP 117 CO 6.20E+01 Gas 1 651 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

LACF Industries

No. 1 Urea 

Boiler CO 6.23E+01 Gas 1 652 NO

OKConocoPhillip

sPoncaCity B-0010 CO 6.59E+01 Gas 1 653 NO

OKConocoPhillip

sPoncaCity B-0009 CO 6.59E+01 Gas 1 654 NO

TXLanxessOrange EQ-2V CO 6.63E+01 Gas 1 655 NO

ILKoppersInc Boiler #1 CO 6.67E+01 Gas 1 656 NO

TXDiamondSha

mrockMcKee

H-45 (#1 

Hydrotreater 

Charge) CO 6.73E+01 Gas 1 657 NO

TXDiamondSha

mrockMcKee

H-1 (#1 Crude 

Charge) CO 6.76E+01 Gas 1 658 NO

CATesoro

S-915 Furnace 

15 CO 7.04E+01 Gas 1 659 NO

WABoeingFredri

ckson Boiler #2 CO 7.06E+01 Gas 1 660 NO

FLIPPensacola

Power Boiler 6 / 

EU ID 03 CO 7.08E+01 Gas 1 661 NO

PADominionGre

enlick Heater A CO 7.10E+01 Gas 1 662 NO

SCPPGSpartanb

urg

LLR01490 

(Superior) CO 7.21E+01 Gas 1 663 NO

TXDowChemical

Freeport2629 BSRSRHET1 CO 7.24E+01 Gas 1 664 NO

NYKodakPark #1 Boiler B-502 CO 7.25E+01 Gas 1 665 NO

VAUniversityofVi

rginia 5575-1-01 CO 7.36E+01 Gas 1 666 NO

PADominionGre

enlick Heater C CO 7.40E+01 Gas 1 667 NO

VAUniversityofVi

rginia 5575-1-04 CO 7.41E+01 Gas 1 668 NO

TXFirestonePoly

mersLLC E-B111 CO 7.41E+01 Gas 1 669 NO

OHMillenniumIn

organicChemical

s1872 B016 CO 7.50E+01 Gas 1 670 NO

LAShellChemica

Geismar Boiler F-U206 CO 7.59E+01 Gas 1 671 NO

ORSPNewsprint B6-EU CO 7.71E+01 Gas 1 672 NO

ORSPNewsprint B7-EU CO 7.71E+01 Gas 1 673 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

OHTateLyleDayt

on B001 CO 7.78E+01 Gas 1 674 NO

PAAKSteelButler 037A - Boiler 21 CO 7.86E+01 Gas 1 675 NO

TXRohmHaasDe

erPark ACET-2A-2 CO 7.99E+01 Gas 1 676 NO

WYOCIWyomin

g Boiler 5 CO 8.03E+01 Gas 1 677 NO

NCReevesBrosR

utherfordton B4 CO 8.30E+01 Gas 1 678 NO

TXDiamondSha

mrockThreeRive

rs 6F-3 CO 8.45E+01 Gas 1 679 NO

TXWesternRefini

ng F-1001 CO 8.71E+01 Gas 1 680 NO

TXDowChemical

Freeport2629 BSRSRHDHT CO 8.99E+01 Gas 1 681 NO

OKTerraNitrogen

#1 Primary 

Reformer CO 9.07E+01 Gas 1 682 NO

MTCHSLaurel14

01 #10 Boiler CO 9.30E+01 Gas 1 683 NO

WYSinclairWyo

ming Pt 41 #9 HPB CO 9.32E+01 Gas 1 684 NO

ILCSLBehring Cogen Turbine CO 9.46E+01 Gas 1 685 NO

INNucorSteel HM#2 Annealing CO 9.60E+01 Gas 1 686 NO

INNucorSteel HM#1 Annealing CO 9.67E+01 Gas 1 687 NO

LACalumet IV-O #10 Boiler CO 9.68E+01 Gas 1 688 NO

TXWesternRefini

ng 125 CO 9.95E+01 Gas 1 689 NO

TXDiamondSha

mrockMcKee

B-12 (600# 

Boiler) CO 9.97E+01 Gas 1 690 NO

TXBayerMaterial

Science

Fulton Hot Oil 

Skid CO 1.00E+02 Gas 1 691 NO

TXGoodyearBea

umont B107 CO 1.00E+02 Gas 1 692 NO

TXLubrizolBaypo

rt BOIL-1 CO 1.02E+02 Gas 1 693 NO

ILTheSolaeCo 606-000 CO 1.02E+02 Gas 1 694 NO

TXTexasPetroch

emicals Boiler No. 2 CO 1.02E+02 Gas 1 695 NO

MNBoisePaper1

212 EU 460 Boiler #9 CO 1.02E+02 Gas 1 696 NO

LALionCopolyme

r EQT 56 CO 1.11E+02 Gas 1 697 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

MOAnheuserBus

ch Boiler 1 CO 1.11E+02 Gas 1 698 NO

NEADMCornPro

cessingColumbu

s WM38 Boiler #1 CO 1.14E+02 Gas 1 699 NO

TXFormosaPlast

ics

THS-10 (EPN 

7F) CO 1.16E+02 Gas 1 700 NO

ILFlintHillsResou

rces HB-2200 CO 1.20E+02 Gas 1 701 NO

ORGPToledo

EU22 - Power 

Boiler #5 CO 1.20E+02 Gas 1 702 NO

WABoeingFredri

ckson Boiler #1 CO 1.30E+02 Gas 1 703 NO

MSPYCO AA-002 CO 1.30E+02 Gas 1 704 NO

COParachuteGa

sPlant H-3741 (HTR-4) CO 1.35E+02 Gas 1 705 NO

PAUnitedRefinin

gWarrant 51 CO 1.36E+02 Gas 1 706 NO

TXDowChemical

Freeport2629 B27P3S523 CO 1.36E+02 Gas 1 707 NO

INHaynesInterna

tional Boiler 1 CO 1.42E+02 Gas 1 708 NO

TXDeerParkRefi

nery H1000 CO 1.44E+02 Gas 1 709 NO

GAADMLocation

551

640- Cleaver 

Brooks CO 1.45E+02 Gas 1 710 NO

CAExxonMobilTorrance 3F-1A CO 1.48E+02 Gas 1 711 NO

CAExxonMobilTorrance 3F-1B CO 1.48E+02 Gas 1 712 NO

CAExxonMobilTorrance 3F-2A CO 1.48E+02 Gas 1 713 NO

CAExxonMobilTorrance 3F-2B CO 1.48E+02 Gas 1 714 NO

MOMcDonnelDo

uglasStLouis 78-1 CO 1.49E+02 Gas 1 715 NO

TXDeerParkRefi

nery H5600 CO 1.55E+02 Gas 1 716 NO

GARobinsAFB B015 CO 1.60E+02 Gas 1 717 NO

MOMcDonnelDo

uglasStLouis 78-2 CO 1.65E+02 Gas 1 718 NO

TXDowChemical

Freeport2629 B23G2S826 CO 1.74E+02 Gas 1 719 NO

PADominionGre

enlick Heater 3 CO 1.80E+02 Gas 1 720 NO

CACAPortlandC

ementMojave D4-1-AH1 CO 1.85E+02 Gas 1 721 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXRohmHaasDe

erPark HT-2 CO 1.86E+02 Gas 1 722 NO

INHaynesInterna

tional Boiler 2 CO 1.88E+02 Gas 1 723 NO

MIPfizerGlobal1

179 EUBoiler1B CO 1.91E+02 Gas 1 724 NO

CADucommunA

eroStructures B003704 CO 2.01E+02 Gas 1 725 NO

MNADMCornDivi

sion

Gas Boiler #4 

EU054 CO 2.02E+02 Gas 1 726 NO

OHHondaMAP

Boiler House 

Boiler 2 CO 2.17E+02 Gas 1 727 NO

INTateLyleSaga

more 21B501 CO 2.17E+02 Gas 1 728 NO

NYKodakPark #3 boiler B-91 CO 2.51E+02 Gas 1 729 NO

ILKoppersInc

Tube Heater 

F201 CO 2.51E+02 Gas 1 730 NO

CAConocoPhillip

sSanFran S# 22 CO 2.54E+02 Gas 1 731 NO

SCMichelinSand

ySprings B:02:01 CO 2.56E+02 Gas 1 732 NO

TXMeadWestva

coEvadale 21-2069 CO 2.59E+02 Gas 1 733 NO

TXLubrizolCorp

DeerParkPlant BOILER NO.5 CO 2.64E+02 Gas 1 734 NO

ORIPSpringfield Package Boiler CO 2.70E+02 Gas 1 735 NO

MIMISugarBayCi

ty #5 Boiler CO 2.84E+02 Gas 1 736 NO

TXDeerParkChe

micalPlant H1300 CO 2.85E+02 Gas 1 737 NO

TXMeadWestva

coEvadale 21-2104 CO 3.18E+02 Gas 1 738 NO

CATesoro

S-931 Furnace 

31 CO 3.68E+02 Gas 1 739 NO

TXRohmHaasDe

erPark HT-1 CO 3.69E+02 Gas 1 740 NO

DEPremcorGrou

pValero 29-H-6 CO 4.07E+02 Gas 1 741 NO

FLPepperidgeFa

rm

HOT WAT GAS 

FIRED CO 4.94E+02 Gas 1 742 NO

TXDiamondSha

mrockMcKee B-6 (Boiler #13) CO 5.17E+02 Gas 1 743 NO

PACraftMaster

No1 Boiler 

Source ID 031 CO 6.00E+02 Gas 1 744 NO

TXTiconaPolyme

rsBishop Power Boiler 12 CO 6.46E+02 Gas 1 745 NO

IDPotlatchLewist

on 4 Power Boiler CO 1.01E+03 Gas 1 746 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

ORGeorgiaPacifi

cWaunaMill

EU34 - Package 

Boiler CO 1.31E+03 Gas 1 747 NO

OHHondaMAP

Boiler House 

Boiler 1 CO 1.33E+03 Gas 1 748 NO

ARGBPMorrilton SN-14 CO 1.68E+03 Gas 1 749 NO

TXOxyVinylsPas

adena F4 Boiler CO 3.22E+03 Gas 1 750 NO

ORGPToledo

EU18 - Power 

Boiler #3 CO 3.35E+03 Gas 1 751 NO

CATesoro

S-917 Furnace 

17 CO 3.40E+03 Gas 1 752 NO

IAAlcoaDavenpo

rt CFRN21 CO 5.83E+03 Gas 1 753 NO

LAShellChemica

Geismar Furnace F-S801 CO 1.29E-02 Gas 2 yes

TXEquistarChem

icals UTBLRG CO 2.11E-02 Gas 2 1 YES

TXFlintHillsPortA

rthur LOUBOILER10 CO 8.00E-02 Gas 2 2 YES

TXEquistarChan

nelview F38001A CO 1.00E-01 Gas 2 3 YES

TXEquistarChan

nelview F38001B CO 1.00E-01 Gas 2 4 YES

TXFlintHillsPortA

rthur LOUBOILER9 CO 1.00E-01 Gas 2 5 YES

TXLyondellChan

nelview F6101 CO 1.00E-01 Gas 2 6 YES

TXLyondellChan

nelview F6105 CO 1.00E-01 Gas 2 7 YES

TXEquistarChan

nelview F4601 CO 1.10E-01 Gas 2 8 YES

TXLyondellChan

nelview F6103 CO 1.10E-01 Gas 2 9 YES

TXLyondellChan

nelview F6104 CO 1.10E-01 Gas 2 10 NO

TXEquistarCorp

usChristi 4D CO 1.35E-01 Gas 2 11 NO

TXLyondellPasa

dena B-901 CO 1.35E-01 Gas 2 12 NO

TXLyondellPasa

dena B-902A CO 1.35E-01 Gas 2 13 NO

TXLyondellPasa

dena B-902B CO 1.35E-01 Gas 2 14 NO

TXChevronBayto

wn H-1530 CO 1.70E-01 Gas 2 15 NO

TXEquistarCorp

usChristi 5A CO 1.80E-01 Gas 2 16 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

TXHuntsmanPor

tNeches

A3 Furnace HA3-1A CO 2.02E-01 Gas 2 17 NO

MDSeverstalSpa

rrows

1BLR (No. 1 

Boiler) CO 2.57E-01 Gas 2 18 NO

LAAmericasStyr

enics HS-4201 CO 3.09E-01 Gas 2 19 NO

LAAmericasStyr

enics HS-4219 CO 3.09E-01 Gas 2 20 NO

INArcelorMittalB

urnsHarbor No. 7 Boiler CO 4.06E-01 Gas 2 21 NO

LAShellChemica

Geismar

Furnace FS2881 CO 5.22E-01 Gas 2 22 NO

TXEquistarCorp

usChristi 4B CO 5.41E-01 Gas 2 23 NO

LAAmericasStyr

enics HS-2201 CO 7.49E-01 Gas 2 24 NO

LAAmericasStyr

enics HS-2219 CO 7.49E-01 Gas 2 25 NO

SCBMWManufa

cturingCo HB03 CO 8.66E-01 Gas 2 26 NO

TXLyondellChan

nelview F6102 CO 8.77E-01 Gas 2 27 NO

TXChevronBayto

wn BF-801A CO 8.90E-01 Gas 2 28 NO

TXEquistarChan

nelview F48001A CO 8.93E-01 Gas 2 29 NO

TXEquistarChan

nelview F48001B CO 8.93E-01 Gas 2 30 NO

TXLyondellChan

nelview F67800 CO 1.00E+00 Gas 2 31 NO

TXLyondellChan

nelview F96800 CO 1.00E+00 Gas 2 32 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1D CO 1.16E+00 Gas 2 33 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1G CO 1.30E+00 Gas 2 34 NO

TXEastmanChe

mLongview OL044H5A CO 1.35E+00 Gas 2 35 NO

TXEquistarChan

nelview F3601 CO 1.62E+00 Gas 2 36 NO

WVMountainStat

eCarbonFollansb

ee S5 CO 2.42E+00 Gas 2 37 NO

MDSeverstalSpa

rrows 3BLR CO 2.71E+00 Gas 2 38 NO

ARAlbemarleSo

uth SN-BH-02 CO 3.12E+00 Gas 2 39 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

WVMountainStat

eCarbonFollansb

ee S1 CO 3.55E+00 Gas 2 40 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1E CO 5.23E+00 Gas 2 41 NO

TXEquistarCorp

usChristi 1J CO 5.23E+00 Gas 2 42 NO

TXFlintHillsPortA

rthur LOUHEATER1 CO 6.00E+00 Gas 2 43 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1B CO 7.71E+00 Gas 2 44 NO

WIGPGreenBay

2818

B29 - Fluidized 

Bed Boiler #9 CO 8.48E+00 Gas 2 45 NO

TXEquistarChem

icals UTBLRH CO 1.04E+01 Gas 2 46 NO

TXEastmanChe

mLongview OL032H5B CO 1.26E+01 Gas 2 47 NO

INRollsRoyceInd

ianapolis 70-65 CO 1.29E+01 Gas 2 48 NO

ARAlbemarleSo

uth SN-BH-01 CO 1.38E+01 Gas 2 49 NO

TXEastmanChe

mLongview OL033H5B CO 1.40E+01 Gas 2 50 NO

TXHuntsmanPor

tNeches Boiler HK-11 CO 1.61E+01 Gas 2 51 NO

LAAmericasStyr

enics HB-302 CO 1.83E+01 Gas 2 52 NO

LALakeCharlesC

hemical

LAB-LH-3 (Hot 

Oil Heater) CO 2.24E+01 Gas 2 53 NO

TXFlintHillsOdes

sa F-Boiler CO 2.34E+01 Gas 2 54 NO

NJAPIFoils 2 CO 2.66E+01 Gas 2 55 NO

TXChevronBayto

wn BA-651 CO 2.80E+01 Gas 2 56 NO

TXChevronBayto

wn BF-801B CO 3.21E+01 Gas 2 57 NO

LAAmericasStyr

enics HS-1101 CO 3.22E+01 Gas 2 58 NO

TXHuntsmanPor

tNeches

PO Boiler H-K2-

003 CO 4.09E+01 Gas 2 59 NO

TXChevronBayto

wn H-3 CO 4.31E+01 Gas 2 60 NO

TXFlintHillsOdes

sa B-Boiler CO 4.98E+01 Gas 2 61 NO

TXEquistarChan

nelview F3701 CO 1.06E+02 Gas 2 62 NO

TXFlintHillsOdes

sa A-Boiler CO 1.08E+02 Gas 2 63 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

INTateLyleSaga

more 21B501 CO 1.23E+02 Gas 2 64 NO

TXGoodyearBea

umont B106 CO 1.32E+02 Gas 2 65 NO

LAGPPortHudso

n

EQT0100 - 

Power Boiler No. 

5 CO 1.38E+02 Gas 2 66 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1H CO 1.70E+02 Gas 2 67 NO

TXChevronBayto

wn BA-401 CO 2.01E+02 Gas 2 68 NO

TXBorger Boiler 1 CO 2.84E+02 Gas 2 69 NO

TXBorger Boiler 2 CO 2.84E+02 Gas 2 70 NO

TXEquistarCorp

usChristi 3A CO 1.35E+03 Gas 2 71 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1J CO 2.75E+03 Gas 2 72 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1C CO 2.87E+03 Gas 2 73 NO

TXHuntsmanPor

tNeches

A3 Furnace HA3-1F CO 3.32E+03 Gas 2 74 NO

SCDAKAmericas P8F CO 5.15E-02 Liquid 1 YES

ORGeorgiaPacifi

cWaunaMill

EU33 - Power 

Boiler CO 1.25E-01 Liquid 2 YES

NJSunocoWestv

ille Boiler #8 CO 1.28E-01 Liquid 3 YES

NJSunocoWestv

ille Boiler #7 CO 1.97E-01 Liquid 4 YES

NENebraskaCity

Station Auxiliary Boiler 2 CO 2.73E-01 Liquid 5 YES

NJSunocoWestv

ille Boiler #5 CO 2.99E-01 Liquid 6 YES

SCGPChemRus

sellville FO Boiler CO 3.73E-01 Liquid 7 YES

NJMerckRahway

E750009 - Boiler 

#9 CO 5.15E-01 Liquid 8 YES

OHOSUColumb

us B140 CO 5.44E-01 Liquid 9 YES

NCCampLejeune

MCB C-CG-650-84B CO 5.67E-01 Liquid 10 YES

VADominionPos

sumPoint Aux. Boiler 001 CO 6.29E-01 Liquid 11 YES

PAKeystonePow

erPlantShelocta Aux Boiler A CO 7.59E-01 Liquid 12 YES

NJSunocoWestv

ille Boiler #6 CO 8.55E-01 Liquid 13 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NCCampLejeune

MCB C-CG-650-83B CO 8.67E-01 Liquid 14 NO

NYConEd59thSt

StationNewYork Boiler 118 CO 1.17E+00 Liquid 15 NO

MEPioneerPlasti

cs Boiler #4 CO 1.28E+00 Liquid 16 NO

NCavoca H-101 CO 1.29E+00 Liquid 17 NO

NCavoca H-102 CO 1.29E+00 Liquid 18 NO

NJMerckRahway

E750010 - Boiler 

#10 CO 1.29E+00 Liquid 19 NO

WI3MMenomoni

e

P04 ABCO east 

boiler CO 1.29E+00 Liquid 20 NO

WI3MMenomoni

e

P05 ABCO west 

boiler CO 1.29E+00 Liquid 21 NO

MANewarkAmeri

ca Boiler #2 CO 1.32E+00 Liquid 22 NO

NJMerckRahway

E750005 - Boiler 

#5 CO 1.33E+00 Liquid 23 NO

OHOSUColumb

us B143 CO 1.40E+00 Liquid 24 NO

GAGPCellulose

Brunswick

U706 -- No. 6 

Power Boiler CO 1.45E+00 Liquid 25 NO

PAUnitedRefinin

gWarrant 55 CO 1.53E+00 Liquid 26 NO

MNMinnesotaSo

ybeanProcessor

s Boiler 1 EU026 CO 1.53E+00 Liquid 27 NO

MNMinnesotaSo

ybeanProcessor

s Boiler 2 EU027 CO 1.53E+00 Liquid 28 NO

INUSSteelGary

Works O4B10459 CO 1.60E+00 Liquid 29 NO

NJMerckRahway

E750003 - Boiler 

#3 CO 1.67E+00 Liquid 30 NO

PAUnitedRefinin

gWarrant 49 CO 1.82E+00 Liquid 31 NO

WVCytec 830X Boiler #1 CO 2.12E+00 Liquid 32 NO

NDADMNorthern

Sun EU62 CO 2.19E+00 Liquid 33 NO

NJChambersCo

gen Auxiliary Boiler CO 2.22E+00 Liquid 34 NO

PACrombyGener

atingStation

033 - Auxiliary 

Boiler CO 2.48E+00 Liquid 35 NO

OHUSEnrichme

ntCorpPiketon

X-6002 Boiler 

No. 2 (South) CO 2.57E+00 Liquid 36 NO

WI3MMenomoni

e

P01 Kewaunee 

steam boiler CO 2.57E+00 Liquid 37 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

PAKeystonePow

erPlantShelocta Aux Boiler B CO 3.16E+00 Liquid 38 NO

MEVersoPaperA

ndroscoggin

Power Boiler No. 

2 CO 3.40E+00 Liquid 39 NO

MEVersoPaperA

ndroscoggin

Power Boiler No. 

1 CO 3.40E+00 Liquid 40 NO

OHUSEnrichme

ntCorpPiketon

X-6002 Boiler 

No. 1 (North) CO 3.85E+00 Liquid 41 NO

PAConemaughP

owerPlantNewFl

orence Aux Boiler B CO 4.17E+00 Liquid 42 NO

TNMilanArmyAm

munitionPlant

D88L-1, Source 

#27-0010-86 CO 4.20E+00 Liquid 43 NO

VABAENorfolk 010 CO 4.29E+00 Liquid 44 NO

CAAerojet

38008 BR 01 

(PO 14611)(C10008) CO 4.33E+00 Liquid 45 NO

VAUniversityofVi

rginia 7103-1-04R CO 4.47E+00 Liquid 46 NO

NJMerckRahway

E750011 - Boiler 

#11 CO 4.87E+00 Liquid 47 NO

MOMcDonnelDo

uglasStLouis 102-5 CO 5.54E+00 Liquid 48 NO

PABoeingRidley

Park 033 CO 5.55E+00 Liquid 49 NO

WI3MMenomoni

e

P02 Kewaunee 

HW boiler CO 5.58E+00 Liquid 50 NO

OHOSUColumb

us B141 CO 5.62E+00 Liquid 51 NO

SCDuPontTeijin

Florence Boiler #1 CO 5.99E+00 Liquid 52 NO

AREvergreenPa

ckaging PB2 CO 6.12E+00 Liquid 53 NO

MDUofMaryland H CO 6.43E+00 Liquid 54 NO

MIPfizerGlobal1

179 EUBoiler5 CO 6.98E+00 Liquid 55 NO

MDUofMaryland B CO 7.72E+00 Liquid 56 NO

NJMerckRahway

E750012 - Boiler 

#12 CO 7.95E+00 Liquid 57 NO

WIWRREnviron

mental B#4 CO 8.08E+00 Liquid 58 NO

MEFPLEnergyW

yman Unit #5 CO 8.20E+00 Liquid 59 NO

FLOkeelanta268 Boiler No. 16 CO 8.39E+00 Liquid 60 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

VANewportNews

ShipbuildingDry

Dock 78-E1 CO 8.71E+00 Liquid 61 NO

TNInvistaChatta

nooga

EU003 - 

Vaporizer #2 CO 9.40E+00 Liquid 62 NO

ILJLMChemicals

BlueIsland Boiler 1 CO 9.66E+00 Liquid 63 NO

SCDuPontTeijin

Florence Boiler #2 CO 9.83E+00 Liquid 64 NO

NJVinelandMuni

ElectricHowardDown Unit 9 CO 1.06E+01 Liquid 65 NO

PAUnitedRefinin

gWarrant 50 CO 1.08E+01 Liquid 66 NO

MDUofMaryland EU 001-4 CO 1.14E+01 Liquid 67 NO

MIConsumerEne

rgyCo-Campbell EUAUXBLR12 CO 1.18E+01 Liquid 68 NO

NJDSMNutrition

al Boiler 4 CO 1.21E+01 Liquid 69 NO

OHOSUColumb

us B142 CO 1.28E+01 Liquid 70 NO

HIPuuneneSuga

rMill Boiler 3 CO 1.33E+01 Liquid 71 NO

WIWRREnviron

mental B#3 CO 1.35E+01 Liquid 72 NO

VAUniversityofVi

rginia 7103-1-03R CO 1.46E+01 Liquid 73 NO

WAGPCamas

No. 5 Power 

Boiler CO 1.74E+01 Liquid 74 NO

WVCytec 831X Boiler #2 CO 1.91E+01 Liquid 75 NO

AREvergreenPa

ckaging PB1 CO 2.10E+01 Liquid 76 NO

MDUofMaryland EU 001-2 CO 2.21E+01 Liquid 77 NO

KSGMFairfax Boiler No.1 CO 2.25E+01 Liquid 78 NO

NDADMNorthern

Sun EU21 CO 2.27E+01 Liquid 79 NO

MN3MCenter EU 043 CO 2.39E+01 Liquid 80 NO

MAUMass EU#7 CO 2.47E+01 Liquid 81 NO

MAMirantCanal Aux Boiler B CO 2.57E+01 Liquid 82 NO

COKodakWinds

or Boiler 71 CO 2.63E+01 Liquid 83 NO

COKodakWinds

or Boiler 72 CO 2.63E+01 Liquid 84 NO

PAAppletonPape

rs #033 CO 3.31E+01 Liquid 85 NO

MAMirantCanal Aux Boiler A CO 3.93E+01 Liquid 86 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 4-CO Floor by 

Fuel

FacilityID

CombustorID_co

mmon

Pollutant_

Name

ppm @ 

3% O2

MACT 

Floor 

FuelCat

Metal 

Furnace? Rank

Test Data in 

Top 12pct

NJDSMNutrition

al Boiler 3 CO 4.15E+01 Liquid 87 NO

IACargillIowaFall

s EP 26 CO 4.34E+01 Liquid 88 NO

NJDSMNutrition

al Boiler 2 CO 4.40E+01 Liquid 89 NO

NCDomtar

66-25-2050 (No. 

1 Package 

Boiler) CO 4.91E+01 Liquid 90 NO

WI3MMenomoni

e

P03 Cleaver 

Brooks HW 

boiler CO 5.45E+01 Liquid 91 NO

MIPfizerGlobal1

179 EUBoiler3 CO 6.15E+01 Liquid 92 NO

PAConemaughP

owerPlantNewFl

orence Aux Boiler A CO 6.18E+01 Liquid 93 NO

MNNSPKingGen

Plant

Auxiliary Boiler 

(EU 028) CO 6.39E+01 Liquid 94 NO

CTElectric Boat EMU 17 CO 7.20E+01 Liquid 95 NO

VAUniversityofVi

rginia 5575-1-02 CO 7.29E+01 Liquid 96 NO

MNGPDuluth EU33 Boiler #3 CO 7.78E+01 Liquid 97 NO

VAUniversityofVi

rginia 5575-1-01 CO 8.02E+01 Liquid 98 NO

VABAENorfolk 009 CO 8.04E+01 Liquid 99 NO

VACloverPower

Station ES-3 CO 8.68E+01 Liquid 100 NO

VAUniversityofVi

rginia 5575-1-03 CO 9.24E+01 Liquid 101 NO

NCInvistaHwy42

1 B7600 CO 9.89E+01 Liquid 102 NO

VAUniversityofVi

rginia 5575-1-04 CO 1.06E+02 Liquid 103 NO

OHSolaeBellvue B010A CO 1.89E+02 Liquid 104 NO

ORIPSpringfield Power Boiler CO 5.52E+02 Liquid 105 NO

MIPfizerGlobal1

179 EUBoiler1B CO 7.46E+02 Liquid 106 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 5-D/F Floor by 

Fuel - Total MASS

FacilityID

CombustorID_com

mon

Pollutant 

Units

MACT 

Floor 

FuelCat

Metal 

Furnace?

Average 

of Test 

Runs

Number of 

Test Runs Rank

Test Data in 

Top 12pct

SCMichelinSandy

Springs B:02:01

ng/dscm 

@ 7% O2 Gas 1 1.26E-01 3 1 YES

WYSinclairWyomi

ng Pt 41 #9 HPB

ng/dscm 

@ 7% O2 Gas 1 1.32E-01 3 2 NO

NCCampLejeune

MCB C-AS-4151-16

ng/dscm 

@ 7% O2 Gas 1 1.38E-01 3 3 NO

WYSinclairWyomi

ng

Pt 74 #2 H2 Plant 

Heater

ng/dscm 

@ 7% O2 Gas 1 1.42E-01 3 4 NO

SCEastmanColom

bia

HTM Heater #3 

(Equip ID 1101)

ng/dscm 

@ 7% O2 Gas 1 1.43E-01 3 5 NO

CTCytecWallingfo

rd 150 Furnace

ng/dscm 

@ 7% O2 Gas 1 1.72E-01 3 6 NO

KSCoffeyvilleRefin

ery EU-39-FH0027

ng/dscm 

@ 7% O2 Gas 1 2.80E-01 3 7 NO

ILUSSGraniteCity

No. 8 Galvanizing 

Line Furnace

ng/dscm 

@ 7% O2 Gas 1 yes 1.27E-02 3 1 YES

CORockyMtnSteel

212

Rod/Bar Mill 

Furnace 

95OPPB088

ng/dscm 

@ 7% O2 Gas 1 yes 4.25E-02 3 2 NO

INOutokumpuStai

nlessPlate

Heppenstall 

Annealing 

Furnace

ng/dscm 

@ 7% O2 Gas 1 yes 4.50E-02 3 3 NO

UTWestinghouse 202

ng/dscm 

@ 7% O2 Gas 1 yes 1.70E-01 3 4 NO

INArcelorMittalBur

nsHarbor

Hot Dip Coating 

Line Annealing 

Furnace

ng/dscm 

@ 7% O2 Gas 1 yes 2.67E-01 3 5 NO

INAlcoaWarrick

Pre-Heat Furnace 

#36

ng/dscm 

@ 7% O2 Gas 1 yes 1.10E+00 3 6 NO

INNucorSteel

Cold Mill 

Annealing

ng/dscm 

@ 7% O2 Gas 1 yes 4.78E+00 3 7 NO

INTateLyleSagam

ore 21B501

ng/dscm 

@ 7% O2 Gas 2 4.50E-02 3 1 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 5-D/F Floor by 

Fuel - Total MASS

FacilityID

CombustorID_com

mon

Pollutant 

Units

MACT 

Floor 

FuelCat

Metal 

Furnace?

Average 

of Test 

Runs

Number of 

Test Runs Rank

Test Data in 

Top 12pct

WVMountainState

CarbonFollansbee S1

ng/dscm 

@ 7% O2 Gas 2 5.20E-02 3 2 NO

SCBMWManufact

uringCo HB03

ng/dscm 

@ 7% O2 Gas 2 9.57E-02 3 3 NO

LAShellChemicaG

eismar Furnace F-S801

ng/dscm 

@ 7% O2 Gas 2 2.31E-01 3 4 NO

MDSeverstalSparr

ows

1BLR (No. 1 

Boiler)

ng/dscm 

@ 7% O2 Gas 2 4.81E-01 3 5 NO

NYConEd59thStSt

ationNewYork Boiler 118

ng/dscm 

@ 7% O2 Liquid 1.77E-03 3 1 YES

CTElectric Boat EMU 17

ng/dscm 

@ 7% O2 Liquid 8.87E-03 3 2 YES

VANewportNewsS

hipbuildingDryDoc

k 78-E1

ng/dscm 

@ 7% O2 Liquid 2.19E-02 3 3 NO

SCGPChemRusse

llville FO Boiler

ng/dscm 

@ 7% O2 Liquid 2.48E-02 3 4 NO

MIConsumerEner

gyCo-Campbell EUAUXBLR12

ng/dscm 

@ 7% O2 Liquid 5.89E-02 3 5 NO

INUSSteelGaryW

orks O4B10459

ng/dscm 

@ 7% O2 Liquid 6.66E-02 3 6 NO

TNMilanArmyAmm

unitionPlant

D88L-1, Source 

#27-0010-86

ng/dscm 

@ 7% O2 Liquid 1.06E-01 3 7 NO

MNGPDuluth EU33 Boiler #3

ng/dscm 

@ 7% O2 Liquid 1.67E-01 3 8 NO

MEFPLEnergyWy

man Unit #5

ng/dscm 

@ 7% O2 Liquid 1.78E-01 3 9 NO

NJVinelandMuniEl

ectricHowardDown Unit 9ng/dscm 

@ 7% O2 Liquid 3.20E-01 3 10 NO

PABoeingRidleyP

ark 033

ng/dscm 

@ 7% O2 Liquid 6.11E-01 3 11 NO

NCInvistaHwy421 B7600

ng/dscm 

@ 7% O2 Liquid 7.54E-01 3 12 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 5-D/F Floor by 

Fuel - Total MASS

FacilityID

CombustorID_com

mon

Pollutant 

Units

MACT 

Floor 

FuelCat

Metal 

Furnace?

Average 

of Test 

Runs

Number of 

Test Runs Rank

Test Data in 

Top 12pct

TNInvistaChattano

oga

EU003 - Vaporizer 

#2

ng/dscm 

@ 7% O2 Liquid 1.19E+00 3 13 NO

SCDAKAmericas P8F

ng/dscm 

@ 7% O2 Liquid 1.47E+01 3 14 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 5-D/F Floor 

by Fuel - TEQ

FacilityID

CombustorID_

common

Pollutant 

Units

MACT 

Floor 

FuelCat

Metal 

Furnace?

Average 

of Test 

Runs

Number of 

Test Runs Rank

Test Data in 

Top 12pct

NCCampLejeu

neMCB C-AS-4151-16

ng/dscm 

@ 7% O2 Gas 1 2.57E-03 3 1 YES

SCMichelinSa

ndySprings B:02:01

ng/dscm 

@ 7% O2 Gas 1 4.25E-03 3 2 NO

SCEastmanCo

lombia

HTM Heater 

#3 (Equip ID 

1101)

ng/dscm 

@ 7% O2 Gas 1 4.27E-03 3 3 NO

WYSinclairWy

oming Pt 41 #9 HPB

ng/dscm 

@ 7% O2 Gas 1 4.40E-03 3 4 NO

WYSinclairWy

oming

Pt 74 #2 H2 

Plant Heater

ng/dscm 

@ 7% O2 Gas 1 5.00E-03 3 5 NO

KSCoffeyvilleR

efinery EU-39-FH0027

ng/dscm 

@ 7% O2 Gas 1 2.52E-02 3 6 NO

CTCytecWallin

gford 150 Furnace

ng/dscm 

@ 7% O2 Gas 1 2.93E+01 3 7 NO

CORockyMtnS

teel212

Rod/Bar Mill 

Furnace 

95OPPB088

ng/dscm 

@ 7% O2 Gas 1 yes 2.58E-03 3 1 YES

INOutokumpu

StainlessPlate

Heppenstall 

Annealing 

Furnace

ng/dscm 

@ 7% O2 Gas 1 yes 3.10E-03 3 2 NO

UTWestinghou

se 202

ng/dscm 

@ 7% O2 Gas 1 yes 6.37E-03 3 3 NO

INArcelorMittal

BurnsHarbor

Hot Dip 

Coating Line 

Annealing 

Furnace

ng/dscm 

@ 7% O2 Gas 1 yes 9.80E-03 3 4 NO

ILUSSGranite

City

No. 8 

Galvanizing 

Line Furnace

ng/dscm 

@ 7% O2 Gas 1 yes 1.92E-02 3 5 NO

INAlcoaWarric

k

Pre-Heat 

Furnace #36

ng/dscm 

@ 7% O2 Gas 1 yes 4.64E-02 3 6 NO

INNucorSteel

Cold Mill 

Annealing

ng/dscm 

@ 7% O2 Gas 1 yes 3.64E-01 3 7 NO

SCBMWManuf

acturingCo HB03

ng/dscm 

@ 7% O2 Gas 2 2.67E-03 3 1 YES
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 5-D/F Floor 

by Fuel - TEQ

FacilityID

CombustorID_

common

Pollutant 

Units

MACT 

Floor 

FuelCat

Metal 

Furnace?

Average 

of Test 

Runs

Number of 

Test Runs Rank

Test Data in 

Top 12pct

INTateLyleSag

amore 21B501

ng/dscm 

@ 7% O2 Gas 2 3.18E-03 3 2 NO

WVMountainSt

ateCarbonFoll

ansbee S1

ng/dscm 

@ 7% O2 Gas 2 5.73E-03 3 3 NO

LAShellChemi

caGeismar

Furnace FS801ng/dscm 

@ 7% O2 Gas 2 1.15E-02 3 4 NO

MDSeverstalS

parrows

1BLR (No. 1 

Boiler)

ng/dscm 

@ 7% O2 Gas 2 2.10E-02 3 5 NO

CTElectric 

Boat EMU 17

ng/dscm 

@ 7% O2 Liquid 1.09E-03 3 1 YES

NYConEd59th

StStationNewY

ork Boiler 118

ng/dscm 

@ 7% O2 Liquid 1.10E-03 3 2 YES

TNMilanArmyA

mmunitionPlan

t

D88L-1, 

Source #27-

0010-86

ng/dscm 

@ 7% O2 Liquid 2.36E-03 3 3 NO

SCGPChemRu

ssellville FO Boiler

ng/dscm 

@ 7% O2 Liquid 2.44E-03 3 4 NO

MEFPLEnergy

Wyman Unit #5

ng/dscm 

@ 7% O2 Liquid 3.66E-03 3 5 NO

MIConsumerE

nergyCoCampbell EUAUXBLR12ng/dscm 

@ 7% O2 Liquid 4.29E-03 3 6 NO

INUSSteelGar

yWorks O4B10459

ng/dscm 

@ 7% O2 Liquid 4.97E-03 3 7 NO

NJVinelandMu

niElectricHowardDown Unit 9ng/dscm 

@ 7% O2 Liquid 5.65E-03 3 8 NO

MNGPDuluth EU33 Boiler #3

ng/dscm 

@ 7% O2 Liquid 1.03E-02 3 9 NO

VANewportNe

wsShipbuilding

DryDock 78-E1

ng/dscm 

@ 7% O2 Liquid 1.16E-02 3 10 NO

PABoeingRidle

yPark 033

ng/dscm 

@ 7% O2 Liquid 1.47E-02 3 11 NO

NCInvistaHwy

421 B7600

ng/dscm 

@ 7% O2 Liquid 1.62E-02 3 12 NO
APPENDIX G-2 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Fuel Type for 

Alternative Solid Waste Definition

Table 5-D/F Floor 

by Fuel - TEQ

FacilityID

CombustorID_

common

Pollutant 

Units

MACT 

Floor 

FuelCat

Metal 

Furnace?

Average 

of Test 

Runs

Number of 

Test Runs Rank

Test Data in 

Top 12pct

TNInvistaChatt

anooga

EU003 - 

Vaporizer #2

ng/dscm 

@ 7% O2 Liquid 5.16E-02 3 13 NO

SCDAKAmeric

as P8F

ng/dscm 

@ 7% O2 Liquid 2.17E-01 3 14 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

FLUSSugarCorp

Boiler No. 

7 CO Biomass

Dutch 

Oven/Susp. 

Burner 1.9.E+01 1 YES

WAGraysHarbor

Paper

No. 6 

Boiler 

(EU2) CO Biomass

Dutch 

Oven/Susp. 

Burner 2.6.E+02 2 YES

FLSugarCaneGro

wersCoop

Boiler No. 

8 CO Biomass

Dutch 

Oven/Susp. 

Burner 3.2.E+02 3 NO

ORRosboroSprin

gfield DV 01.1 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.1.E+02 4 NO

FLUSSugarCorp

Boiler No. 

8 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.5.E+02 5 NO

MNNorbordMinne

sota

Konus No. 

1 CO Biomass

Dutch 

Oven/Susp. 

Burner 9.6.E+02 6 NO

MNNorbordMinne

sota

Konus No. 

2 CO Biomass

Dutch 

Oven/Susp. 

Burner 9.6.E+02 7 NO

FLUSSugarCorp

Boiler No. 

4 CO Biomass

Dutch 

Oven/Susp. 

Burner 1.5.E+03 8 NO

FLSugarCaneGro

wersCoop

Boiler No. 

1 CO Biomass

Dutch 

Oven/Susp. 

Burner 2.4.E+03 9 NO

FLOsceolaFarms

Boiler No. 

3 CO Biomass

Dutch 

Oven/Susp. 

Burner 4.3.E+03 10 NO

FLUSSugarCorp

Boiler No. 

1 CO Biomass

Dutch 

Oven/Susp. 

Burner 7.4.E+03 11 NO

FLOsceolaFarms

Boiler No. 

6 CO Biomass

Dutch 

Oven/Susp. 

Burner 7.5.E+03 12 NO

FLUSSugarCorp

Boiler No. 

2 CO Biomass

Dutch 

Oven/Susp. 

Burner 2.0.E+04 13 NO

NDCargillWestFa

rgo

Foster 

Wheeler 

Boiler 

(EU43) CO Biomass FB 3.6.E+03 1 YES

KYWeyerhaeuser

EKY MP 01-01 CO Biomass Fuel Cell 5.7.E+01 1 YES

KYWeyerhaeuser

EKY MP 01-03 CO Biomass Fuel Cell 5.7.E+01 2 YES

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

ARWeyerhaeuser

DierksMill SN-45 CO Biomass Fuel Cell 6.2.E+01 3 YES

WAWeyerhaeuse

r_Raymond

Hog Fuel 

Boiler 

EU1 CO Biomass Fuel Cell 1.2.E+02 4 YES

MSWeyerhaeuse

rBruce

AA-002 

No. 2 

Boiler CO Biomass Fuel Cell 1.9.E+02 5 YES

GAADMLocation

551

630- 

Wellons CO Biomass Fuel Cell 3.7.E+02 6 NO

ORWeyerhaeuse

rCoWarrentonLu

mberMill 3-HFB CO Biomass Fuel Cell 4.5.E+02 7 NO

ARAnthonyForest

Products SN-16 CO Biomass Fuel Cell 5.4.E+02 8 NO

ARAnthonyForest

Products SN-12 CO Biomass Fuel Cell 6.5.E+02 9 NO

TXNorbordTexas

Nacogdoches

Konus No. 

1 CO Biomass Fuel Cell 1.2.E+03 10 NO

TXNorbordTexas

Nacogdoches

Konus No. 

2 CO Biomass Fuel Cell 1.2.E+03 11 NO

IDChilcoLakeSaw

mill HFB1 CO Biomass

Stoker/SlopedG

rate/Other 5.1.E+01 1 YES

ARWestFraserHu

ttig SN-24 CO Biomass

Stoker/SlopedG

rate/Other 6.5.E+01 2 YES

MILPCSagola

TOHWood CO Biomass

Stoker/SlopedG

rate/Other 6.8.E+01 3 YES

INConsolidatedG

rainandBarge P17B CO Biomass

Stoker/SlopedG

rate/Other 8.7.E+01 4 YES

INConsolidatedG

rainandBarge P17C CO Biomass

Stoker/SlopedG

rate/Other 8.7.E+01 5 YES

MNAndersonCor

pBayport

Boiler 11 

EU620 CO Biomass

Stoker/SlopedG

rate/Other 9.3.E+01 6 YES

MNAndersonCor

pBayport

Boiler 12 

EU621 CO Biomass

Stoker/SlopedG

rate/Other 1.0.E+02 7 YES

MSGPNewAugus

ta

AA-015 

Power 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 1.0.E+02 8 YES

ALMeadwestvaco

Cottonton46

No.3 

Wood 

Residue 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 1.2.E+02 9 YES
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

MSShuqualakLu

mber

Boiler 4 

(AA-108) CO Biomass

Stoker/SlopedG

rate/Other 1.2.E+02 10 NO

OHAkronThermal

Energy

Unit #2 

(B004) CO Biomass

Stoker/SlopedG

rate/Other 1.3.E+02 11 NO

ORBlueHeronPa

per G Boiler CO Biomass

Stoker/SlopedG

rate/Other 1.5.E+02 12 NO

MIWhitePineElec

tric

IBW 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 1.5.E+02 13 NO

ALWestervelt

Teaford - 

Unit 003 CO Biomass

Stoker/SlopedG

rate/Other 1.6.E+02 14 NO

ALIPCourtland

No. 1 

Combinati

on Boiler / 

11CU101 CO Biomass

Stoker/SlopedG

rate/Other 1.6.E+02 15 NO

IDRileyCreekLum

ber HFB1 CO Biomass

Stoker/SlopedG

rate/Other 1.6.E+02 16 NO

ARDelticTimber

Waldo

Wood 

Fired 

Boiler No. 

1 (SN-13) CO Biomass

Stoker/SlopedG

rate/Other 2.0.E+02 17 NO

MNDESPHansO

Nyman EU007 CO Biomass

Stoker/SlopedG

rate/Other 2.0.E+02 18 NO

GAADMLocation

551

B115ANorth 

Hurst CO Biomass

Stoker/SlopedG

rate/Other 2.3.E+02 19 NO

TXAnthonyForest

Prod-ATL

EP 11.1 

Hurst CO Biomass

Stoker/SlopedG

rate/Other 2.3.E+02 20 NO

ARLeolaLumber

Mill SN-01A CO Biomass

Stoker/SlopedG

rate/Other 2.4.E+02 21 NO

ALMeadwestvaco

Cottonton46

No.2 

Wood 

Residue 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 2.6.E+02 22 NO

ARDelticTimber

Waldo

Wood 

Fired 

Boiler No. 

2 (SN-14) CO Biomass

Stoker/SlopedG

rate/Other 2.7.E+02 23 NO

GARayonierBaxle

y PB02 CO Biomass

Stoker/SlopedG

rate/Other 2.7.E+02 24 NO

GAADMLocation

551

B115BSouth 

Hurst CO Biomass

Stoker/SlopedG

rate/Other 2.7.E+02 25 NO

ARPotlatchForest

Warren

Wellons 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 2.9.E+02 26 NO

ARGBPMorrilton SN-04 CO Biomass

Stoker/SlopedG

rate/Other 2.9.E+02 27 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

ORJeldWenKlam

anthFalls BLRG CO Biomass

Stoker/SlopedG

rate/Other 3.0.E+02 28 NO

TXAnthonyForest

Prod-ATL

EP 10.1 

Superior CO Biomass

Stoker/SlopedG

rate/Other 3.0.E+02 29 NO

FLGPPalatka EU16 CO Biomass

Stoker/SlopedG

rate/Other 3.0.E+02 30 NO

GARayonierJesu

pMill PB03 CO Biomass

Stoker/SlopedG

rate/Other 3.5.E+02 31 NO

FLSmurfit-Stone 5PB CO Biomass

Stoker/SlopedG

rate/Other 3.9.E+02 32 NO

ARLeolaLumber

Mill SN-01B CO Biomass

Stoker/SlopedG

rate/Other 3.9.E+02 33 NO

ALWestervelt

Wellons - 

Unit 001 CO Biomass

Stoker/SlopedG

rate/Other 4.3.E+02 34 NO

LAWeyerhaeuser

Dodson

ES-017 

WFB CO Biomass

Stoker/SlopedG

rate/Other 4.3.E+02 35 NO

ARWestFraserHu

ttig SN-01 CO Biomass

Stoker/SlopedG

rate/Other 4.8.E+02 36 NO

MSGPBaySpring

s

AA-001 

(Boiler No. 

1) CO Biomass

Stoker/SlopedG

rate/Other 5.5.E+02 37 NO

TXwestfraser Boiler-1 CO Biomass

Stoker/SlopedG

rate/Other 5.7.E+02 38 NO

MSGPBaySpring

s

AA-003 

(Boiler No. 

2) CO Biomass

Stoker/SlopedG

rate/Other 5.9.E+02 39 NO

ARDelticTimberO

la

Wood 

Fired 

Boiler at 

Ola Mill 

(SN-13) CO Biomass

Stoker/SlopedG

rate/Other 6.2.E+02 40 NO

WILPHayward

K2 Line 1 

Konus CO Biomass

Stoker/SlopedG

rate/Other 7.4.E+02 41 NO

TXMeadWestvac

oEvadale 21-2105 CO Biomass

Stoker/SlopedG

rate/Other 7.5.E+02 42 NO

ARWeyerhaeuser

DierksMill SN-32 CO Biomass

Stoker/SlopedG

rate/Other 8.2.E+02 43 NO

GAGPCelluloseB

runswick

U700 -- 

No. 4 

Power 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 9.2.E+02 44 NO

ARGBPMorrilton SN-02 CO Biomass

Stoker/SlopedG

rate/Other 1.1.E+03 45 NO

WILPHayward

K1 Line 1 

Konus CO Biomass

Stoker/SlopedG

rate/Other 1.2.E+03 46 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

LAHoodIndustrie

s

EQT001 

(woodfired boiler 

No. 1) CO Biomass

Stoker/SlopedG

rate/Other 1.2.E+03 47 NO

LAGPPortHudso

n

EQT0099 -

Combinati

on Boiler 

No. 1 CO Biomass

Stoker/SlopedG

rate/Other 1.3.E+03 48 NO

IDRileyCreekLum

ber HFB2 CO Biomass

Stoker/SlopedG

rate/Other 1.3.E+03 49 NO

ALManningtonW

oodFloors BB01 CO Biomass

Stoker/SlopedG

rate/Other 1.3.E+03 50 NO

ALManningtonW

oodFloors BB02 CO Biomass

Stoker/SlopedG

rate/Other 1.3.E+03 51 NO

LABoiseCascade

Oakdale B-1 CO Biomass

Stoker/SlopedG

rate/Other 1.4.E+03 52 NO

LAWestFraserJo

yce 74A CO Biomass

Stoker/SlopedG

rate/Other 1.6.E+03 53 NO

WILPHayward

K4 Line 2 

Konus CO Biomass

Stoker/SlopedG

rate/Other 1.6.E+03 54 NO

LAWestFraserJo

yce 75A CO Biomass

Stoker/SlopedG

rate/Other 1.7.E+03 55 NO

IDMoyieSprings 

Lumber420 HFB1 CO Biomass

Stoker/SlopedG

rate/Other 1.9.E+03 56 NO

MSWeyerhaeuse

rBruce

AA-001 

No. 1 

Boiler CO Biomass

Stoker/SlopedG

rate/Other 2.0.E+03 57 NO

LAHoodIndustrie

s

EQT002 

(woodfired boiler 

No. 2) CO Biomass

Stoker/SlopedG

rate/Other 2.3.E+03 58 NO

LAWestFraserJo

yce 74B CO Biomass

Stoker/SlopedG

rate/Other 2.3.E+03 59 NO

WILPHayward

K3 Line 2 

Konus CO Biomass

Stoker/SlopedG

rate/Other 2.4.E+03 60 NO

MSWeyerhaeuse

r1398

Boiler No. 

1 CO Biomass

Stoker/SlopedG

rate/Other 2.9.E+03 61 NO

GAPCAValdosta 1005 CO Biomass

Stoker/SlopedG

rate/Other 3.4.E+03 62 NO

GAPCAValdosta 1006 CO Biomass

Stoker/SlopedG

rate/Other 3.4.E+03 63 NO

HIPuuneneSugar

Mill Boiler 1 CO Biomass

Stoker/SlopedG

rate/Other 3.7.E+03 64 NO

HIPuuneneSugar

Mill Boiler 2 CO Biomass

Stoker/SlopedG

rate/Other 3.7.E+03 65 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

ORBBSMMedfor

d B1 CO Biomass

Stoker/SlopedG

rate/Other 3.9.E+03 66 NO

ORBBSMMedfor

d B2 CO Biomass

Stoker/SlopedG

rate/Other 3.9.E+03 67 NO

ORBBSMMedfor

d B3 CO Biomass

Stoker/SlopedG

rate/Other 3.9.E+03 68 NO

WABoiseKettleFa

llsPlywood B1 CO Biomass

Stoker/SlopedG

rate/Other 5.5.E+03 69 NO

GAWestFraserFo

lkston FOB1 CO Biomass

Stoker/SlopedG

rate/Other 9.5.E+03 70 NO

GAWestFraserFo

lkston FOB2 CO Biomass

Stoker/SlopedG

rate/Other 1.3.E+04 71 NO

IAADMCornProc

essingCR EU-530 CO Coal FB 8.3.E+00 1 YES

IAADMCornProc

essingCR EU-501B CO Coal FB 1.8.E+01 2 YES

IAADMCornProc

essingCR EU-502A CO Coal FB 2.2.E+01 3 YES

IAADMCornProc

essingCR EU-501A CO Coal FB 3.0.E+01 4 YES

INPurdueUniveris

ity Boiler 5 CO Coal FB 3.1.E+01 5 YES

ILPolyOne B1 CO Coal FB 3.9.E+01 6 NO

NCUNCCogen ES-001 CO Coal FB 4.1.E+01 7 NO

NEADMLincoln

EU26 

Coal 

Boiler CO Coal FB 4.3.E+01 8 NO

ILBungeDanville

CFB 

Boiler CO Coal FB 4.9.E+01 9 NO

IAADMCornProc

essingCR EU-502B CO Coal FB 5.0.E+01 10 NO

IAUofIowa

EP7 Boiler 

11 CO Coal FB 5.1.E+01 11 NO

IAArchersDaniels

MidlandDesMoin

es

Asea 

Boiler #1 CO Coal FB 5.5.E+01 12 NO

ILDukeEnergyTu

scola Unit 3 CO Coal PC 5.5.E-02 1 YES

ILDukeEnergyTu

scola Unit 4 CO Coal PC 5.5.E-02 2 YES

ILDukeEnergyTu

scola Unit 1 CO Coal PC 5.7.E-02 3 YES

VAPhilipMorrisPa

rk500 B2 CO Coal PC 1.4.E+00 4 YES

AZCatalystPaper

Snowflake

Power 

Boiler #2 

Coal CO Coal PC 2.2.E+00 5 YES
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

OKGPMuskogee

Mill B-3 CO Coal PC 3.2.E+00 6 NO

ILPrairiePowerPe

arl B1 CO Coal PC 6.8.E+00 7 NO

INTateLyleSaga

more 31B1 CO Coal PC 6.8.E+00 8 NO

VAPhilipMorrisPa

rk500 B3 CO Coal PC 8.8.E+00 9 NO

IAUofNorthernIo

wa Boiler #3 CO Coal PC 1.0.E+01 10 NO

TNDuPontOldHic

koryPlant #20 Boiler CO Coal PC 1.1.E+01 11 NO

INNewEnergy

Riley 

Boiler CO Coal PC 1.2.E+01 12 NO

INNewEnfergy

Riley 

Boiler CO Coal PC 1.2.E+01 13 NO

NCBlueRidgePap

er G11040 CO Coal PC 1.3.E+01 14 NO

OKGPMuskogee

Mill B-4 CO Coal PC 1.4.E+01 15 NO

INAlcoaWarrick Unit #3 CO Coal PC 1.4.E+01 16 NO

NCBlueRidgePap

er G11039 CO Coal PC 1.5.E+01 17 NO

NCBlueRidgePap

er G11038 CO Coal PC 1.6.E+01 18 NO

VASmurfitStone

Westpt PB08 CO Coal PC 1.6.E+01 19 NO

TNEastman_NO_

CBIDATA Boiler 30 CO Coal PC 1.8.E+01 20 NO

NCMillerCoors

ES-2 

Coal/No. 2 

& 6 Fuel 

Oil Boiler CO Coal PC 1.8.E+01 21 NO

IDTASCOPaul

Erie City 

Boiler CO Coal PC 1.9.E+01 22 NO

VAPhilipMorrisM

C PC CO Coal PC 2.0.E+01 23 NO

WYFMCGreenRi

ver NS-1A CO Coal PC 2.1.E+01 24 NO

SCInternationalP

aperEastover

No. 1 

Power 

Boiler CO Coal PC 2.6.E+01 25 NO

OKGPMuskogee

Mill B-2 CO Coal PC 2.7.E+01 26 NO

WYGeneralChem

ical

GR-2-L (C 

BOILER) CO Coal PC 3.0.E+01 27 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

VAGPBigIsland2

703

PWR04 - 

No. 4 

Power 

Boiler CO Coal PC 3.4.E+01 28 NO

VAINVISTAWayn

esboro

2-205 

(B#2) 

Boiler #2 CO Coal PC 4.1.E+01 29 NO

INAlcoaWarrick Unit #2 CO Coal PC 4.3.E+01 30 NO

PADomtarJohnso

nburg

#81 Coal 

Boiler CO Coal PC 6.8.E+01 31 NO

PADomtarJohnso

nburg

#82 Coal 

Boiler CO Coal PC 6.8.E+01 32 NO

NCBlueRidgePap

er G11037 CO Coal PC 7.5.E+01 33 NO

MITBSimonPowe

rPlant Unit 1 CO Coal PC 7.9.E+01 34 NO

MOAnheuserBus

ch Boiler 5 CO Coal PC 1.1.E+02 35 NO

WVPPGMartinsvi

lle

R011-

Boiler 3 CO Coal PC 1.3.E+02 36 NO

MDNewPageLuke No. 25 CO Coal PC 1.3.E+02 37 NO

MOAnheuserBus

ch Boiler 1 CO Coal PC 1.4.E+02 38 NO

ALIPCourtland

No.2 

Combinati

on Boiler / 

11CU201 CO Coal PC 1.7.E+02 39 NO

INNotreDame B-4 CO Coal

Stoker/SlopedG

rate/Other 4.3.E+00 1 YES

OHMortonSaltRitt

man

B002 - 

Coal-Fired 

Boiler #2 CO Coal

Stoker/SlopedG

rate/Other 1.5.E+01 2 YES

WVDuPontWashi

ngtonWorks P05 CO Coal

Stoker/SlopedG

rate/Other 1.6.E+01 3 YES

OHAppletonIdeas

Boiler 4 

(B003) CO Coal

Stoker/SlopedG

rate/Other 2.0.E+01 4 YES

OHAkronThermal

Energy

Boiler #32 

(B001) CO Coal

Stoker/SlopedG

rate/Other 2.5.E+01 5 YES

PABellefieldPlant Boiler 1 CO Coal

Stoker/SlopedG

rate/Other 2.5.E+01 6 YES

NCNC_DukeUniv

ersity_Durham 7754-03 CO Coal

Stoker/SlopedG

rate/Other 2.8.E+01 7 NO

PABellefieldPlant Boiler 5 CO Coal

Stoker/SlopedG

rate/Other 3.8.E+01 8 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

IAMuscatinePow

erandWater Unit 7 CO Coal

Stoker/SlopedG

rate/Other 4.2.E+01 9 NO

VAUniversityofVir

ginia

7103-1-

01R CO Coal

Stoker/SlopedG

rate/Other 4.4.E+01 10 NO

OHAppletonIdeas

Boiler 2 

(B002) CO Coal

Stoker/SlopedG

rate/Other 4.6.E+01 11 NO

PABayValleyFoo

dsPittsburgh

Boiler No. 

3 CO Coal

Stoker/SlopedG

rate/Other 5.2.E+01 12 NO

PABayValleyFoo

dsPittsburgh

Boiler No. 

4 CO Coal

Stoker/SlopedG

rate/Other 5.2.E+01 13 NO

KYISPChemicals

0AA 

(Riley) CO Coal

Stoker/SlopedG

rate/Other 5.2.E+01 14 NO

ILAbbottAbbottPa

rk Unit 5AP CO Coal

Stoker/SlopedG

rate/Other 5.4.E+01 15 NO

MOColumbiaPow

erPlant

Boiler Unit 

6 CO Coal

Stoker/SlopedG

rate/Other 6.5.E+01 16 NO

MOColumbiaPow

erPlant

Boiler Unit 

7 CO Coal

Stoker/SlopedG

rate/Other 6.5.E+01 17 NO

NCNC_DukeUniv

ersity_Durham 7754-02 CO Coal

Stoker/SlopedG

rate/Other 6.9.E+01 18 NO

VAUniversityofVir

ginia

7103-1-

02R CO Coal

Stoker/SlopedG

rate/Other 7.3.E+01 19 NO

PABellefieldPlant Boiler 3 CO Coal

Stoker/SlopedG

rate/Other 7.6.E+01 20 NO

IAUofIowa

EP6 Boiler 

10 CO Coal

Stoker/SlopedG

rate/Other 9.0.E+01 21 NO

WVATKRocketC

enter

NB2766 

W-17479-

W (Boiler 

17) CO Coal

Stoker/SlopedG

rate/Other 9.0.E+01 22 NO

SCClemson 04-B04 CO Coal

Stoker/SlopedG

rate/Other 9.6.E+01 23 NO

OHBataviaTrans

missions

Boiler 2 

(B002) CO Coal

Stoker/SlopedG

rate/Other 1.0.E+02 24 NO

NDMinnDakFarm

ers

Babcock 

and 

Wilcox 

Boiler #5 CO Coal

Stoker/SlopedG

rate/Other 1.1.E+02 25 NO

PABayValleyFoo

dsPittsburgh

Boiler No. 

1 CO Coal

Stoker/SlopedG

rate/Other 1.4.E+02 26 NO

PABayValleyFoo

dsPittsburgh

Boiler No. 

2 CO Coal

Stoker/SlopedG

rate/Other 1.4.E+02 27 NO

VAUniversityofVir

ginia 7103-1-05 CO Coal

Stoker/SlopedG

rate/Other 1.5.E+02 28 NO

WYFMCGranger UIN-14 CO Coal

Stoker/SlopedG

rate/Other 1.6.E+02 29 NO

WIThilmanyPape

rsNicoletMill B23 CO Coal

Stoker/SlopedG

rate/Other 2.1.E+02 30 NO
FacilityID

Combusto

rID_comm

on

Pollutant_

Name

MACT 

Floor 

FuelCat

Combustor 

Design

ppm @3% 

O2 Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor 

Design for Alternative Solid Waste Definition

Table 9: CO Floor by Combustor

WIThilmanyPape

rsNicoletMill B24 CO Coal

Stoker/SlopedG

rate/Other 2.1.E+02 31 NO

WYFMCGranger UIN-15 CO Coal

Stoker/SlopedG

rate/Other 2.4.E+02 32 NO

MNADMCornDivi

sion

Coal 

Boiler #1 

EU049 CO Coal

Stoker/SlopedG

rate/Other 2.5.E+02 33 NO

MNADMCornDivi

sion

Coal 

Boiler #2 

EU050 CO Coal

Stoker/SlopedG

rate/Other 2.5.E+02 34 NO

MDNewPageLuke No. 24 CO CoalStoker/SlopedG

rate/Other 2.9.E+02 35 NO

OHCampbellsSo

upCo B001 CO Coal

Stoker/SlopedG

rate/Other 3.8.E+02 36 NO

OHCampbellsSo

upCo B002 CO Coal

Stoker/SlopedG

rate/Other 3.8.E+02 37 NO

TNCargillMemphi

s

Stoker 

Boiler 

8001 CO Coal

Stoker/SlopedG

rate/Other 5.5.E+02 38 NO

IDTASCOPaul

Babcock 

and 

Wilcox 

(B&W) 

Boiler CO Coal

Stoker/SlopedG

rate/Other 5.8.E+02 39 NO

MNBlandinPaper

EnergyCtr #5 Boiler CO Coal

Stoker/SlopedG

rate/Other 8.4.E+02 40 NO

MNBlandinPaper

EnergyCtr #6 Boiler CO Coal

Stoker/SlopedG

rate/Other 8.4.E+02 41 NO

MIMortonSaltMan

istee

No. 6 

Boiler CO Coal

Stoker/SlopedG

rate/Other 1.3.E+03 42 NO

IACargillEddyville 1.001 CO Coal

Stoker/SlopedG

rate/Other 4.4.E+03 43 NO

IACargillEddyville 1.002 CO Coal

Stoker/SlopedG

rate/Other 4.4.E+03 44 NO

IACargillEddyville 1.039 CO Coal

Stoker/SlopedG

rate/Other 4.4.E+03 45 NO
FacilityID CombustorID_common

MACT 

Floor 

FuelCat

Combusto

r Design

Pollutant 

Units

Average of 

Test Runs Rank

Test Data in 

Top 12pct

ORRosboroSpri

ngfield DV 01.1 Biomass

Dutch 

Oven/Sus

p. Burner

ng/dscm 

@ 7% O2 9.12E+00 1 YES

WAGraysHarbo

rPaper No. 6 Boiler (EU2) Biomass

Dutch 

Oven/Sus

p. Burner

ng/dscm 

@ 7% O2 1.71E+01 2 NO

NDCargillWest

Fargo

Foster Wheeler Boiler 

(EU43) Biomass FB

ng/dscm 

@ 7% O2 1.83E-01 1 YES

ARWeyerhaeus

erDierksMill SN-45 Biomass Fuel Cell

ng/dscm 

@ 7% O2 1.79E-02 1 YES

WAWeyerhaeu

ser_Raymond Hog Fuel Boiler EU1 Biomass Fuel Cell

ng/dscm 

@ 7% O2 3.19E-02 2 YES

MSWeyerhaeu

serBruce AA-002 No. 2 Boiler Biomass Fuel Cell

ng/dscm 

@ 7% O2 1.67E-01 3 YES

ORWeyerhaeu

serCoWarrento

nLumberMill 3-HFB Biomass Fuel Cell

ng/dscm 

@ 7% O2 3.07E-01 4 YES

ARAnthonyFor

estProducts SN-12 Biomass Fuel Cell

ng/dscm 

@ 7% O2 5.65E-01 5 YES

ARPotlatchFor

estWarren Wellons Boiler Biomass

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 5.84E-02 1 YES

ARGBPMorrilto

n SN-04 Biomass

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 1.76E+00 2 NO

GAGPCellulose

Brunswick

U700 -- No. 4 Power 

Boiler Biomass

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 1.90E+00 3 NO

INPurdueUnive

risity Boiler 5 Coal FB

ng/dscm 

@ 7% O2 1.91E-03 1 YES

IARoquetteAm

erica

Circulating Fluidized Bed 

Boiler (121) Coal FB

ng/dscm 

@ 7% O2 1.66E-02 2 YES

IAUofIowa EP7 Boiler 11 Coal FB

ng/dscm 

@ 7% O2 9.59E-02 3 YES

IAADMCornPro

cessingCR EU-501B Coal FB

ng/dscm 

@ 7% O2 9.77E-02 4 YES

ILPolyOne B1 Coal FB

ng/dscm 

@ 7% O2 1.50E-01 5 YES

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor Design for Alternative 

Solid Waste Definition

Table 10: D/F Total Mass Floor by Combustor
FacilityID CombustorID_common

MACT 

Floor 

FuelCat

Combusto

r Design

Pollutant 

Units

Average of 

Test Runs Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor Design for Alternative 

Solid Waste Definition

Table 10: D/F Total Mass Floor by Combustor

IAArchersDanie

lsMidlandDesM

oines Asea Boiler #1 Coal FB

ng/dscm 

@ 7% O2 2.37E-01 6 NO

ILBungeDanvill

e CFB Boiler Coal FB

ng/dscm 

@ 7% O2 3.42E-01 7 NO

NCUNCCogen ES-001 Coal FB

ng/dscm 

@ 7% O2 2.06E+00 8 NO

WVPPGMartin

sville R011-Boiler 3 Coal PC

ng/dscm 

@ 7% O2 1.82E-02 1 YES

NCMillerCoors

ES-2 Coal/No. 2 & 6 

Fuel Oil Boiler Coal PC

ng/dscm 

@ 7% O2 1.91E-02 2 NO

INTateLyleSag

amore 31B1 Coal PC

ng/dscm 

@ 7% O2 4.80E-02 3 NO

VASmurfitSton

eWestpt PB08 Coal PC

ng/dscm 

@ 7% O2 1.59E-01 4 NO

TNEastman_N

O_CBIDATA Boiler 30 Coal PC

ng/dscm 

@ 7% O2 2.70E-01 5 NO

MITBSimonPo

werPlant Unit 1 Coal PC

ng/dscm 

@ 7% O2 6.21E-01 6 NO

IAUofNorthernI

owa Boiler #3 Coal PC

ng/dscm 

@ 7% O2 9.00E-01 7 NO

VAINVISTAWa

ynesboro 2-205 (B#2) Boiler #2 Coal PC

ng/dscm 

@ 7% O2 2.31E+00 8 NO

KYISPChemica

ls 0AA (Riley) Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 2.53E-03 1 YES

WINewPageBir

on B24 Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 1.24E-02 2 NO

ILAbbottAbbott

Park Unit 5AP Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 1.51E-02 3 NO

INNotreDame B-4 Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 4.93E-02 4 NO

TNCargillMemp

his Stoker Boiler 8001 Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 5.05E-02 5 NO

WVATKRocket

Center

NB2766 W-17479-W 

(Boiler 17) Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 9.69E-02 6 NO

OHMortonSalt

Rittman

B002 - Coal-Fired Boiler 

#2 Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 2.41E-01 7 NO
FacilityID CombustorID_common

MACT 

Floor 

FuelCat

Combusto

r Design

Pollutant 

Units

Average of 

Test Runs Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor Design for Alternative 

Solid Waste Definition

Table 10: D/F Total Mass Floor by Combustor

VAUniversityof

Virginia 7103-1-01R Coal

Stoker/Slo

pedGrate/

Other

ng/dscm 

@ 7% O2 3.75E+00 8 NO
FacilityID

CombustorID_co

mmon

MACT 

Floor 

FuelCat

Combusto

r Design

ng/dscm 

@7% O2

Number of 

Test Runs Rank

Test Data in 

Top 12pct

ORRosboroSprin

gfield DV 01.1 Biomass

Dutch 

Oven/Sus

p. Burner 9.53E-02 3 1 YES

WAGraysHarbor

Paper

No. 6 Boiler 

(EU2) Biomass

Dutch 

Oven/Sus

p. Burner 3.67E-01 3 2 NO

NDCargillWestF

argo

Foster Wheeler 

Boiler (EU43) Biomass FB 1.09E-02 3 1 YES

WAWeyerhaeus

er_Raymond

Hog Fuel Boiler 

EU1 Biomass Fuel Cell 2.42E-04 3 1 YES

MSWeyerhaeuse

rBruce

AA-002 No. 2 

Boiler Biomass Fuel Cell 3.35E-03 3 2 YES

ORWeyerhaeuse

rCoWarrentonLu

mberMill 3-HFB Biomass Fuel Cell 4.46E-03 1 3 YES

ARWeyerhaeuse

rDierksMill SN-45 Biomass Fuel Cell 8.48E-03 3 4 YES

ARAnthonyFores

tProducts SN-12 Biomass Fuel Cell 1.03E-02 3 5 YES

ARGBPMorrilton SN-04 Biomass

Stoker/Slo

pedGrate/

Other 1.52E-05 3 1 YES

ARPotlatchFores

tWarren Wellons Boiler Biomass

Stoker/Slo

pedGrate/

Other 1.06E-02 3 2 NO

GAGPCelluloseB

runswick

U700 -- No. 4 

Power Boiler Biomass

Stoker/Slo

pedGrate/

Other 2.59E-02 3 3 NO

INPurdueUniveri

sity Boiler 5 Coal FB 9.33E-04 3 1 YES

IARoquetteAmeri

ca

Circulating 

Fluidized Bed 

Boiler (121) Coal FB 1.10E-03 3 2 YES

IAArchersDaniel

sMidlandDesMoi

nes Asea Boiler #1 Coal FB 3.13E-03 3 3 YES

IAUofIowa EP7 Boiler 11 Coal FB 3.56E-03 3 4 YES

ILPolyOne B1 Coal FB 7.37E-03 3 5 YES

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor Design for 

Alternative Solid Waste Definition

Table 11: D/F TEQ Floor by Combustor
FacilityID

CombustorID_co

mmon

MACT 

Floor 

FuelCat

Combusto

r Design

ng/dscm 

@7% O2

Number of 

Test Runs Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor Design for 

Alternative Solid Waste Definition

Table 11: D/F TEQ Floor by Combustor

IAADMCornProc

essingCR EU-501B Coal FB 1.30E-02 3 6 NO

ILBungeDanville CFB Boiler Coal FB 1.57E-02 3 7 NO

NCUNCCogen ES-001 Coal FB 3.42E-02 3 8 NO

WVPPGMartinsv

ille R011-Boiler 3 Coal PC 2.12E-03 3 1 YES

NCMillerCoors

ES-2 Coal/No. 2 

& 6 Fuel Oil 

Boiler Coal PC 2.43E-03 3 2 NO

VASmurfitStone

Westpt PB08 Coal PC 3.25E-03 3 3 NO

INTateLyleSaga

more 31B1 Coal PC 5.42E-03 3 4 NO

TNEastman_NO

_CBIDATA Boiler 30 Coal PC 6.55E-03 3 5 NO

IAUofNorthernIo

wa Boiler #3 Coal PC 2.02E-02 3 6 NO

MITBSimonPow

erPlant Unit 1 Coal PC 4.59E-02 3 7 NO

VAINVISTAWay

nesboro

2-205 (B#2) 

Boiler #2 Coal PC 1.21E-01 3 8 NO

WINewPageBiro

n B24 Coal

Stoker/Slo

pedGrate/

Other 1.52E-03 3 1 YES

ILAbbottAbbottP

ark Unit 5AP Coal

Stoker/Slo

pedGrate/

Other 2.13E-03 3 2 NO

KYISPChemicals 0AA (Riley) Coal

Stoker/Slo

pedGrate/

Other 2.85E-03 3 3 NO

WVATKRocketC

enter

NB2766 W17479-W (Boiler 

17) Coal

Stoker/Slo

pedGrate/

Other 2.87E-03 3 4 NO

TNCargillMemph

is

Stoker Boiler 

8001 Coal

Stoker/Slo

pedGrate/

Other 3.45E-03 3 5 NO

OHMortonSaltRit

tman

B002 - CoalFired Boiler #2 Coal

Stoker/Slo

pedGrate/

Other 4.94E-03 3 6 NO

INNotreDame B-4 Coal

Stoker/Slo

pedGrate/

Other 7.18E-03 3 7 NO
FacilityID

CombustorID_co

mmon

MACT 

Floor 

FuelCat

Combusto

r Design

ng/dscm 

@7% O2

Number of 

Test Runs Rank

Test Data in 

Top 12pct

APPENDIX G-3 Emission Test and Fuel Analysis Data Ranked for MACT Floor Analysis According to Combustor Design for 

Alternative Solid Waste Definition

Table 11: D/F TEQ Floor by Combustor

VAUniversityofVi

rginia 7103-1-01R Coal

Stoker/Slo

pedGrate/

Other 3.55E-02 3 8 NO
Appendix G-4: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

TestDate_co

mmon

Has Total 

Mass ND 

Data?

Total Mass 

PCDD/PCDF 

Unit

Test 

Burning 

Waste 

under Alt 

Defn?

Total Mass 

PCDD/PCDF 

YES Biomass

Dutch Oven/Susp. Burner 1

ORRosboroSpringfield DV 01.1 M23-1 7/23/2009 DLL

ng/dscm @ 7% O2 1.34E+01 

YES Biomass

Dutch Oven/Susp. Burner 1

ORRosboroSpringfield DV 01.1 M23-2 7/23/2009 DLL

ng/dscm @ 7% O2 6.47E+00 

YES Biomass

Dutch Oven/Susp. Burner 1

ORRosboroSpringfield DV 01.1 M23-3 7/24/2009 DLL

ng/dscm @ 7% O2 7.48E+00 

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Sample #1 8/27/2009 DLL

ng/dscm @ 7% O2 4.76E-01 

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Sample #2 8/29/2009 DLL

ng/dscm @ 7% O2 3.57E-02 

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Sample #3 8/29/2009 DLL

ng/dscm @ 7% O2 3.76E-02 

YES Biomass Fuel Cell 1

ARWeyerhaeuserDierksMill SN-45 Sample #1 7/17/2009 DLL

ng/dscm @ 7% O2 2.01E-02 

YES Biomass Fuel Cell 1

ARWeyerhaeuserDierksMill SN-45 Sample #2 7/17/2009 DLL

ng/dscm @ 7% O2 3.85E-04 

YES Biomass Fuel Cell 1

ARWeyerhaeuserDierksMill SN-45 Sample #3 7/20/2009 DLL

ng/dscm @ 7% O2 3.31E-02 

YES Biomass Fuel Cell 2

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Sample #1 8/12/2009 DLL

ng/dscm @ 7% O2 3.85E-02 

YES Biomass Fuel Cell 2

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Sample #2 8/13/2009

ng/dscm @ 7% O2 3.78E-02 
Appendix G-4: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

TestDate_co

mmon

Has Total 

Mass ND 

Data?

Total Mass 

PCDD/PCDF 

Unit

Test 

Burning 

Waste 

under Alt 

Defn?

Total Mass 

PCDD/PCDF 

YES Biomass Fuel Cell 2

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Sample #3 8/13/2009 DLL

ng/dscm @ 7% O2 1.94E-02 

YES Biomass Fuel Cell 3

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Sample #1 8/4/2009 DLL

ng/dscm @ 7% O2 2.14E-01 

YES Biomass Fuel Cell 3

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Sample #2 8/4/2009 DLL

ng/dscm @ 7% O2 1.36E-01 

YES Biomass Fuel Cell 3

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Sample #3 8/4/2009 DLL

ng/dscm @ 7% O2 1.51E-01 

YES Biomass Fuel Cell 4

ORWeyerhaeuserCoWarrentonLumberMill 3-HFB Sample #2 8/6/2009

ng/dscm @ 7% O2 3.07E-01 

YES Biomass Fuel Cell 5

ARAnthonyForestProducts SN-12 Sample #1 9/2/2009 DLL

ng/dscm @ 7% O2 4.97E-01 

YES Biomass Fuel Cell 5

ARAnthonyForestProducts SN-12 Sample #2 9/2/2009 DLL

ng/dscm @ 7% O2 3.58E-01 

YES Biomass Fuel Cell 5

ARAnthonyForestProducts SN-12 Sample #3 9/3/2009 DLL

ng/dscm @ 7% O2 8.40E-01 

YES Biomass

Stoker/SlopedGrate/Other 1

ARPotlatchForestWarren

Wellons Boiler 1 9/3/2009

ng/dscm @ 7% O2 9.07E-02 

YES Biomass

Stoker/SlopedGrate/Other 1

ARPotlatchForestWarren

Wellons Boiler 2 9/4/2009 DLL

ng/dscm @ 7% O2 2.70E-02 

YES Biomass

Stoker/SlopedGrate/Other 1

ARPotlatchForestWarren

Wellons Boiler 3 9/4/2009 DLL

ng/dscm @ 7% O2 5.76E-02 

YES Coal FB 1

INPurdueUniverisity Boiler 5 Sample #1 7/22/2009 DLL

ng/dscm @ 7% O2 2.18E-03 
Appendix G-4: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

TestDate_co

mmon

Has Total 

Mass ND 

Data?

Total Mass 

PCDD/PCDF 

Unit

Test 

Burning 

Waste 

under Alt 

Defn?

Total Mass 

PCDD/PCDF 

YES Coal FB 1

INPurdueUniverisity Boiler 5 Sample #2 7/23/2009 DLL

ng/dscm @ 7% O2 1.74E-03 

YES Coal FB 1

INPurdueUniverisity Boiler 5 Sample #3 7/23/2009 DLL

ng/dscm @ 7% O2 1.82E-03 

YES Coal FB 2

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Sample #1 6/4/2009 DLL

ng/dscm @ 7% O2 3.18E-02 

YES Coal FB 2

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Sample #2 6/5/2009 DLL

ng/dscm @ 7% O2 1.51E-02 

YES Coal FB 2

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Sample #3 6/5/2009 DLL

ng/dscm @ 7% O2 2.78E-03 

YES Coal FB 3 IAUofIowa

EP7 Boiler 11 4 8/6/2009

ng/dscm @ 7% O2 9.96E-02 

YES Coal FB 3 IAUofIowa

EP7 Boiler 11 5 8/6/2009

ng/dscm @ 7% O2 1.17E-01 

YES Coal FB 3 IAUofIowa

EP7 Boiler 11 6 8/7/2009

ng/dscm @ 7% O2 7.11E-02 

YES Coal FB 4

IAADMCornProcessingCR EU-501B Sample #1 8/11/2009

ng/dscm @ 7% O2 1.10E-01 

YES Coal FB 4

IAADMCornProcessingCR EU-501B Sample #2 8/11/2009

ng/dscm @ 7% O2 7.60E-02 

YES Coal FB 4

IAADMCornProcessingCR EU-501B Sample #3 8/12/2009

ng/dscm @ 7% O2 1.07E-01 

YES Coal FB 5 ILPolyOne B1 1 9/10/2009

ng/dscm @ 7% O2 1.26E-01 

YES Coal FB 5 ILPolyOne B1 2 9/11/2009

ng/dscm @ 7% O2 1.91E-01 

YES Coal FB 5 ILPolyOne B1 3 9/11/2009

ng/dscm @ 7% O2 1.32E-01 
Appendix G-4: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

TestDate_co

mmon

Has Total 

Mass ND 

Data?

Total Mass 

PCDD/PCDF 

Unit

Test 

Burning 

Waste 

under Alt 

Defn?

Total Mass 

PCDD/PCDF 

YES Coal PC 1

WVPPGMartinsville

R011-Boiler 3 Sample #1 7/22/2009 DLL

ng/dscm @ 7% O2 2.52E-02 

YES Coal PC 1

WVPPGMartinsville

R011-Boiler 3 Sample #2 7/23/2009 DLL

ng/dscm @ 7% O2 1.41E-02 

YES Coal PC 1

WVPPGMartinsville

R011-Boiler 3 Sample #3 7/23/2009 DLL

ng/dscm @ 7% O2 1.52E-02 

YES Coal

Stoker/SlopedGrate/Other 1

KYISPChemicals 0AA (Riley) Sample #1 11/17/2009

ng/dscm @ 7% O2 3.20E-03 

YES Coal

Stoker/SlopedGrate/Other 1

KYISPChemicals 0AA (Riley) Sample #2 11/17/2009

ng/dscm @ 7% O2 2.30E-03 

YES Coal

Stoker/SlopedGrate/Other 1

KYISPChemicals 0AA (Riley) Sample #3 11/18/2009

ng/dscm @ 7% O2 2.10E-03 
Appendix G-5: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Top 12 

pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common TestID

TestDate_co

mmon

Has Total 

Mass ND 

Data?

Total Mass 

PCDD/PCDF 

Unit

Test Burning 

Waste under Alt 

Defn?

Total M

PCDD/

YES Gas 1 1

SCMichelinSandySprings B:02:01 Sample #1 9/10/2009 DLL

ng/dscm @ 7% O2 1.2

YES Gas 1 1

SCMichelinSandySprings B:02:01 Sample #2 9/10/2009 DLL

ng/dscm @ 7% O2 1.1

YES Gas 1 1

SCMichelinSandySprings B:02:01 Sample #3 9/10/2009 DLL

ng/dscm @ 7% O2 1.3

YES Gas 1 yes 1

ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Sample #1 8/25/2009 BDL

ng/dscm @ 7% O2 1.2

YES Gas 1 yes 1

ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Sample #2 8/25/2009 DLL

ng/dscm @ 7% O2 1.2

YES Gas 1 yes 1

ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Sample #3 8/26/2009 BDL

ng/dscm @ 7% O2 1.2

YES Gas 2 1

INTateLyleSagamore 21B501 Sample #1 8/25/2009 DLL

ng/dscm @ 7% O2 6.4

YES Gas 2 1

INTateLyleSagamore 21B501 Sample #2 8/26/2009 DLL

ng/dscm @ 7% O2 2.4

YES Gas 2 1

INTateLyleSagamore 21B501 Sample #3 8/27/2009 DLL

ng/dscm @ 7% O2 4.6

YES Liquid 1

NYConEd59thStStationNewYork Boiler 118 Sample #1 8/19/2009 DLL

ng/dscm @ 7% O2 2.0

YES Liquid 1

NYConEd59thStStationNewYork Boiler 118 Sample #2 8/19/2009 DLL

ng/dscm @ 7% O2 1.9

YES Liquid 1

NYConEd59thStStationNewYork Boiler 118 Sample #3 8/19/2009 DLL

ng/dscm @ 7% O2 1.3

YES Liquid 2

CTElectric Boat EMU 17 Sample #1 8/19/2009

ng/dscm @ 7% O2 9.9
Appendix G-5: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Top 12 

pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common TestID

TestDate_co

mmon

Has Total 

Mass ND 

Data?

Total Mass 

PCDD/PCDF 

Unit

Test Burning 

Waste under Alt 

Defn?

Total M

PCDD/

YES Liquid 2

CTElectric Boat EMU 17 Sample #2 8/20/2009

ng/dscm @ 7% O2 8.8

YES Liquid 2

CTElectric Boat EMU 17 Sample #3 8/20/2009

ng/dscm @ 7% O2 7.9
Appendix G-6: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

Has TEQ ND 

Data?

Test Burning 

Waste under Alt 

Defn?

ng/dscm@7% O2

ln(ng/dscm@7

% O2)

YES Biomass

Dutch Oven/Susp. Burner 1

ORRosboroSpringfield DV 01.1 M23-1 DLL 1.34E-01 -2.01E+0

YES Biomass

Dutch Oven/Susp. Burner 1

ORRosboroSpringfield DV 01.1 M23-2 DLL 7.15E-02 -2.64E+0

YES Biomass

Dutch Oven/Susp. Burner 1

ORRosboroSpringfield DV 01.1 M23-3 DLL 8.03E-02 -2.52E+0

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Sample #1 DLL 2.74E-02 -3.60E+0

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Sample #2 DLL 2.54E-03 -5.98E+0

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Sample #3 DLL 2.58E-03 -5.96E+0

YES Biomass Fuel Cell 1

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Sample #1 DLL 2.45E-04 -8.31E+0

YES Biomass Fuel Cell 1

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Sample #2 2.71E-04 -8.21E+0

YES Biomass Fuel Cell 1

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 Sample #3 DLL 2.09E-04 -8.47E+0

YES Biomass Fuel Cell 2

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Sample #1 DLL 4.06E-03 -5.51E+0

YES Biomass Fuel Cell 2

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Sample #2 DLL 2.78E-03 -5.89E+0

YES Biomass Fuel Cell 2

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler Sample #3 DLL 3.21E-03 -5.74E+0
Appendix G-6: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

Has TEQ ND 

Data?

Test Burning 

Waste under Alt 

Defn?

ng/dscm@7% O2

ln(ng/dscm@7

% O2)

YES Biomass Fuel Cell 3

ORWeyerhaeuserCoWarrentonLumberMill 3-HFB Sample #2 4.46E-03 -5.41E+0

YES Biomass Fuel Cell 4

ARWeyerhaeuserDierksMill SN-45 Sample #1 DLL 1.47E-02 -4.22E+0

YES Biomass Fuel Cell 4

ARWeyerhaeuserDierksMill SN-45 Sample #2 DLL 2.88E-05 -1.05E+0

YES Biomass Fuel Cell 4

ARWeyerhaeuserDierksMill SN-45 Sample #3 DLL 1.07E-02 -4.54E+0

YES Biomass Fuel Cell 5

ARAnthonyForestProducts SN-12 Sample #1 DLL 1.48E-02 -4.21E+0

YES Biomass Fuel Cell 5

ARAnthonyForestProducts SN-12 Sample #2 DLL 5.51E-03 -5.20E+0

YES Biomass Fuel Cell 5

ARAnthonyForestProducts SN-12 Sample #3 DLL 1.07E-02 -4.54E+0

YES Biomass

Stoker/SlopedGrate/Other 1

ARGBPMorrilton SN-04 1 DLL 2.20E-05 -1.07E+0

YES Biomass

Stoker/SlopedGrate/Other 1

ARGBPMorrilton SN-04 2 1.16E-05 -1.14E+0

YES Biomass

Stoker/SlopedGrate/Other 1

ARGBPMorrilton SN-04 3 DLL 1.20E-05 -1.13E+0

YES Coal FB 1

INPurdueUniverisity Boiler 5 Sample #1 DLL 8.43E-04 -7.08E+0

YES Coal FB 1

INPurdueUniverisity Boiler 5 Sample #2 DLL 9.55E-04 -6.95E+0

YES Coal FB 1

INPurdueUniverisity Boiler 5 Sample #3 DLL 1.00E-03 -6.91E+0
Appendix G-6: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

Has TEQ ND 

Data?

Test Burning 

Waste under Alt 

Defn?

ng/dscm@7% O2

ln(ng/dscm@7

% O2)

YES Coal FB 2

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Sample #1 DLL 1.41E-03 -6.56E+0

YES Coal FB 2

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Sample #2 DLL 1.02E-03 -6.89E+0

YES Coal FB 2

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Sample #3 DLL 8.76E-04 -7.04E+0

YES Coal FB 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Sample #1 2.22E-03 -6.11E+0

YES Coal FB 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Sample #2 3.94E-03 -5.54E+0

YES Coal FB 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Sample #3 3.25E-03 -5.73E+0

YES Coal FB 4 IAUofIowa

EP7 Boiler 11 4 4.01E-03 -5.52E+0

YES Coal FB 4 IAUofIowa

EP7 Boiler 11 5 3.57E-03 -5.64E+0

YES Coal FB 4 IAUofIowa

EP7 Boiler 11 6 3.09E-03 -5.78E+0

YES Coal FB 5 ILPolyOne B1 1 7.40E-03 -4.91E+0YES Coal FB 5 ILPolyOne B1 2 7.72E-03 -4.86E+0YES Coal FB 5 ILPolyOne B1 3 6.98E-03 -4.96E+0YES Coal PC 1

WVPPGMartinsville

R011-Boiler 3 Sample #1 DLL 2.44E-03 -6.02E+0

YES Coal PC 1

WVPPGMartinsville

R011-Boiler 3 Sample #2 DLL 2.07E-03 -6.18E+0

YES Coal PC 1

WVPPGMartinsville

R011-Boiler 3 Sample #3 DLL 1.86E-03 -6.29E+0
Appendix G-6: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Top 12 

pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common TestID

Has TEQ ND 

Data?

Test Burning 

Waste under Alt 

Defn?

ng/dscm@7% O2

ln(ng/dscm@7

% O2)

YES Coal

Stoker/SlopedGrate/Other 1

WINewPageBiron B24 Sample #1 DLL 1.35E-03 -6.60E+0

YES Coal

Stoker/SlopedGrate/Other 1

WINewPageBiron B24 Sample #2 DLL 1.78E-03 -6.33E+0

YES Coal

Stoker/SlopedGrate/Other 1

WINewPageBiron B24 Sample #3 DLL 1.42E-03 -6.55E+0
Appendix G-7: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Top 12 

pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common TestID

Has TEQ ND 

Data?

Test Burning 

Waste under Alt 

Defn?

ng/dscm@7% O2

ln(ng/dscm@

O2)

YES Gas 1 1

NCCampLejeuneMCB

C-AS-4151-16 Sample #1 3.73E-03 -5.59E

YES Gas 1 1

NCCampLejeuneMCB

C-AS-4151-16 Sample #2 1.27E-03 -6.67E

YES Gas 1 1

NCCampLejeuneMCB

C-AS-4151-16 Sample #3 2.70E-03 -5.92E

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 M23-1 DLL 2.70E-03 -5.92E

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 M23-2 DLL 2.33E-03 -6.06E

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 M23-3 DLL 2.70E-03 -5.91E

YES Gas 2 1

SCBMWManufacturingCo HB03 Sample #1 DLL 2.21E-03 -6.11E

YES Gas 2 1

SCBMWManufacturingCo HB03 Sample #2 DLL 3.80E-03 -5.57E

YES Gas 2 1

SCBMWManufacturingCo HB03 Sample #3 DLL 2.00E-03 -6.22E

YES Liquid 1

CTElectric Boat EMU 17 Sample #1 1.18E-03 -6.75E

YES Liquid 1

CTElectric Boat EMU 17 Sample #2 1.08E-03 -6.83E

YES Liquid 1

CTElectric Boat EMU 17 Sample #3 1.03E-03 -6.88E

YES Liquid 2

NYConEd59thStStationNewYork Boiler 118 Sample #1 DLL 1.28E-03 -6.66E

YES Liquid 2

NYConEd59thStStationNewYork Boiler 118 Sample #2 DLL 1.23E-03 -6.70E

YES Liquid 2

NYConEd59thStStationNewYork Boiler 118 Sample #3 DLL 7.90E-04 -7.14E
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 11/13/2007 5.00E-03 -5.30E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/5/2009 2.00E-04 -8.52E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 8/5/2009 2.00E-04 -8.52E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 11/13/2007 4.10E-03 -5.50E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/6/2009 9.00E-04 -7.01E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 8/6/2009 9.00E-04 -7.01E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 11/13/2007 7.10E-03 -4.95E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/6/2009 5.00E-04 -7.60E+00

YES Biomass 1

GAGPCelluloseBrunswick

U700 -- No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 8/6/2009 5.00E-04 -7.60E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #1 4/22/2008 2.00E-03 -6.21E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #1 4/23/2008 6.00E-04 -7.42E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #1 8/8/2008 7.00E-03 -4.96E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #2 8/8/2008 9.00E-03 -4.71E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #2 4/22/2008 1.00E-03 -6.91E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #2 4/23/2008 8.00E-04 -7.13E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #3 4/23/2008 4.00E-04 -7.82E+00

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #3 8/8/2008 1.30E-02 -4.34E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 2

MNAndersonCorpBayport

Boiler 11 EU620

Particulate Matter (PM) filterable Sample #3 4/22/2008 2.00E-03 -6.21E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #1 8/8/2008 7.00E-03 -4.96E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #1 4/23/2008 6.00E-04 -7.42E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #1 4/22/2008 2.00E-03 -6.21E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #2 4/23/2008 8.00E-04 -7.13E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #2 4/22/2008 1.00E-03 -6.91E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #2 8/8/2008 9.00E-03 -4.71E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #3 8/8/2008 1.30E-02 -4.34E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #3 4/23/2008 4.00E-04 -7.82E+00

YES Biomass 3

MNAndersonCorpBayport

Boiler 12 EU621

Particulate Matter (PM) filterable Sample #3 4/22/2008 2.00E-03 -6.21E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #1 11/10/2004 7.00E-04 -7.26E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #1 8/11/2009 ND 1.50E-03 -6.50E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #1 9/18/1996 2.00E-03 -6.21E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #2 8/11/2009 1.80E-03 -6.32E+00

YES Biomass 4

WAWeyerhaeuser_Raym

ond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #2 9/18/1996 2.00E-03 -6.21E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #2 11/10/2004 7.00E-04 -7.26E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #3 9/18/1996 2.00E-03 -6.21E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #3 8/12/2009 ND 6.00E-04 -7.42E+00

YES Biomass 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1

Particulate Matter (PM) filterable Sample #3 11/10/2004 5.00E-04 -7.60E+00

YES Biomass 5

ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable 1 9/9/2009 4.80E-03 -5.34E+00

YES Biomass 5

ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable 2 9/9/2009 3.30E-03 -5.71E+00

YES Biomass 5

ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable 3 9/10/2009 3.55E-02 -3.34E+00

YES Biomass 5

ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable Sample #1 8/8/2006 1.10E-03 -6.81E+00

YES Biomass 5

ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable Sample #2 8/8/2006 7.00E-04 -7.26E+00

YES Biomass 5

ARPotlatchForestWarren

Wellons Boiler

Particulate Matter (PM) filterable Sample #3 8/8/2006 6.00E-04 -7.42E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #1 8/7/1997 2.43E-02 -3.72E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #1 12/5/2002 1.30E-03 -6.65E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #1 7/22/2009 3.19E-03 -5.75E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #2 8/7/1997 1.28E-02 -4.36E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #2 12/5/2002 1.50E-03 -6.50E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #2 7/23/2009 3.87E-03 -5.55E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #3 7/23/2009 4.17E-03 -5.48E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #3 8/7/1997 9.70E-03 -4.64E+00

YES Biomass 6

ARWeyerhaeuserDierksMill SN-45

Particulate Matter (PM) filterable Sample #3 12/5/2002 1.30E-03 -6.65E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/4/2002 5.40E-03 -5.22E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 8/11/1997 1.94E-02 -3.94E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/5/2001 1.10E-02 -4.51E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 9/29/2004 2.70E-03 -5.91E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/4/2003 2.30E-03 -6.07E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 11/21/1998 5.80E-03 -5.15E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 11/9/2000 3.50E-03 -5.65E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #1 12/10/1999 1.60E-02 -4.14E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 11/21/1998 5.80E-03 -5.15E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/10/1999 1.00E-02 -4.61E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 11/9/2000 1.70E-03 -6.38E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/4/2002 4.80E-03 -5.34E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/4/2003 1.50E-03 -6.50E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 9/29/2004 3.60E-03 -5.63E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 8/11/1997 1.47E-02 -4.22E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #2 12/5/2001 6.40E-03 -5.05E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/10/1999 1.50E-02 -4.20E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/4/2002 4.30E-03 -5.45E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 9/29/2004 4.90E-03 -5.32E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/4/2003 1.40E-03 -6.57E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 12/5/2001 2.74E-02 -3.60E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 8/11/1997 8.60E-03 -4.76E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 11/9/2000 1.80E-03 -6.32E+00

YES Biomass 7

ARWeyerhaeuserDierksMill SN-32

Particulate Matter (PM) filterable Sample #3 11/21/1998 4.20E-03 -5.47E+00

YES Biomass 8

MSGPNewAugusta

AA-015 Power Boiler

Particulate Matter (PM) filterable Sample #1 7/12/2006 2.80E-03 -5.88E+00

YES Biomass 8

MSGPNewAugusta

AA-015 Power Boiler

Particulate Matter (PM) filterable Sample #2 7/12/2006 1.00E-03 -6.91E+00

YES Biomass 8

MSGPNewAugusta

AA-015 Power Boiler

Particulate Matter (PM) filterable Sample #3 7/12/2006 1.60E-03 -6.44E+00

YES Biomass 9

IDRileyCreekLumber HFB1

Particulate Matter (PM) filterable Sample #1 4/24/2003 3.04E-03 -5.80E+00

YES Biomass 9

IDRileyCreekLumber HFB1

Particulate Matter (PM) filterable Sample #2 4/24/2003 1.85E-03 -6.29E+00

YES Biomass 9

IDRileyCreekLumber HFB1

Particulate Matter (PM) filterable Sample #3 4/24/2003 1.45E-03 -6.53E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 3/24/2005 4.30E-03 -5.45E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 11/30/2007 1.60E-02 -4.14E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 3/26/2005 3.40E-03 -5.68E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 6/2/2006 1.90E-03 -6.27E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 1/10/2006 1.90E-02 -3.96E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 8/22/2006 1.01E-02 -4.60E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #1 1/5/2007 1.00E-02 -4.61E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 3/26/2005 6.80E-03 -4.99E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 6/2/2006 2.60E-03 -5.95E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 11/30/2007 1.10E-02 -4.51E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 1/10/2006 2.00E-02 -3.91E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 1/5/2007 8.00E-03 -4.83E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 8/22/2006 1.93E-02 -3.95E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #2 3/24/2005 3.40E-03 -5.68E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 8/22/2006 1.67E-02 -4.09E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 3/26/2005 7.80E-03 -4.85E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 1/5/2007 1.10E-02 -4.51E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 1/10/2006 2.40E-02 -3.73E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 3/24/2005 4.10E-03 -5.50E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 6/2/2006 2.20E-03 -6.12E+00

YES Biomass 10

FLUSSugarCorp Boiler No. 8

Particulate Matter (PM) filterable Sample #3 11/30/2007 1.70E-02 -4.07E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 11

FLSmurfitStone 5PB

Particulate Matter (PM) filterable Sample #1 7/10/2007 4.00E-03 -5.52E+00

YES Biomass 11

FLSmurfitStone 5PB

Particulate Matter (PM) filterable Sample #2 7/10/2007 1.00E-03 -6.91E+00

YES Biomass 11

FLSmurfitStone 5PB

Particulate Matter (PM) filterable Sample #3 7/10/2007 3.00E-03 -5.81E+00

YES Biomass 12

WIDomtar2814 B11, S11

Particulate Matter (PM) filterable Sample #1 8/29/2007 1.00E-03 -6.91E+00

YES Biomass 12

WIDomtar2814 B11, S11

Particulate Matter (PM) filterable Sample #2 8/29/2007 2.60E-03 -5.95E+00

YES Biomass 12

WIDomtar2814 B11, S11

Particulate Matter (PM) filterable Sample #3 8/29/2007 5.70E-03 -5.17E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 7/11/2003 3.80E-03 -5.57E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 8/5/2009 7.40E-03 -4.91E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 8/23/1999 9.40E-03 -4.67E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 2/26/1993 1.30E-03 -6.65E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 6/28/2005 4.00E-03 -5.52E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 2/22/2006 8.00E-03 -4.83E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #1 8/31/2007 7.80E-03 -4.85E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 8/5/2009 8.40E-03 -4.78E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 8/23/1999 1.30E-02 -4.34E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 2/26/1993 3.80E-03 -5.57E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 6/28/2005 4.00E-03 -5.52E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 2/22/2006 6.40E-03 -5.05E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 7/11/2003 3.90E-03 -5.55E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #2 8/31/2007 4.00E-04 -7.82E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 6/28/2005 5.00E-03 -5.30E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 2/22/2006 8.60E-03 -4.76E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 7/11/2003 2.90E-03 -5.84E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 8/31/2007 3.70E-03 -5.60E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 2/26/1993 4.90E-03 -5.32E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 8/23/1999 8.00E-03 -4.83E+00

YES Biomass 13

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler

Particulate Matter (PM) filterable Sample #3 8/5/2009 4.40E-03 -5.43E+00

YES Coal 1

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Particulate Matter (PM) filterable Sample #1 6/3/2008 7.06E-04 -7.26E+00

YES Coal 1

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Particulate Matter (PM) filterable Sample #1 8/26/2009 2.00E-04 -8.52E+00

YES Coal 1

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Particulate Matter (PM) filterable Sample #2 6/3/2008 5.34E-04 -7.53E+00

YES Coal 1

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Particulate Matter (PM) filterable Sample #2 8/26/2009 2.00E-04 -8.52E+00

YES Coal 1

IAArchersDanielsMidland

DesMoines

Asea Boiler #1

Particulate Matter (PM) filterable Sample #3 6/3/2008 5.37E-04 -7.53E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 1

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Particulate Matter (PM) filterable Sample #3 8/27/2009 2.00E-04 -8.52E+00

YES Coal 2

IAUofNorthernIowa Boiler #3

Particulate Matter (PM) filterable 4 10/6/2009 7.97E-04 -7.13E+00

YES Coal 2

IAUofNorthernIowa Boiler #3

Particulate Matter (PM) filterable 5 10/6/2009 6.03E-04 -7.41E+00

YES Coal 2

IAUofNorthernIowa Boiler #3

Particulate Matter (PM) filterable 6 10/7/2009 3.73E-04 -7.89E+00

YES Coal 3

VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable M027-1 9/17/2009 1.27E-03 -6.67E+00

YES Coal 3

VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable M027-2 9/17/2009 4.51E-04 -7.70E+00

YES Coal 3

VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable M027-3 9/18/2009 7.12E-04 -7.25E+00

YES Coal 3

VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable Sample #1 12/6/2007 9.00E-04 -7.01E+00

YES Coal 3

VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable Sample #2 12/6/2007 5.00E-04 -7.60E+00

YES Coal 3

VAUniversityofVirginia 7103-1-01R

Particulate Matter (PM) filterable Sample #3 12/6/2007 4.00E-04 -7.82E+00

YES Coal 4

IAIAStateUnivPowerPlant B2

Particulate Matter (PM) filterable Sample #1 3/27/2008 5.05E-04 -7.59E+00

YES Coal 4

IAIAStateUnivPowerPlant B2

Particulate Matter (PM) filterable Sample #2 3/27/2008 1.00E-03 -6.91E+00

YES Coal 4

IAIAStateUnivPowerPlant B2

Particulate Matter (PM) filterable Sample #3 3/27/2008 3.18E-04 -8.05E+00

YES Coal 5

WIGreenBayPackagingMillDivision

Boiler B26- Coal Fired Boiler

Particulate Matter (PM) filterable Sample #1 5/16/2006 1.07E-03 -6.84E+00

YES Coal 5

WIGreenBayPackagingMillDivision

Boiler B26- Coal Fired Boiler

Particulate Matter (PM) filterable Sample #2 5/16/2006 4.00E-05 -1.01E+01

YES Coal 5

WIGreenBayPackagingMillDivision

Boiler B26- Coal Fired Boiler

Particulate Matter (PM) filterable Sample #3 5/16/2006 8.10E-04 -7.12E+00

YES Coal 6

TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable 1 8/5/2009 7.14E-04 -7.24E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 6

TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable 2 11/6/2009 7.81E-04 -7.15E+00

YES Coal 6

TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable 3 8/6/2009 DLL 6.40E-04 -7.35E+00

YES Coal 6

TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable Sample #1 7/17/2007 2.10E-02 -3.86E+00

YES Coal 6

TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable Sample #2 7/17/2007 1.78E-02 -4.03E+00

YES Coal 6

TNCargillMemphis

Stoker Boiler 8001

Particulate Matter (PM) filterable Sample #3 7/17/2007 1.33E-02 -4.32E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 8/20/1996 1.69E-02 -4.08E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 11/9/2004 1.30E-03 -6.65E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 8/8/2000 6.40E-02 -2.75E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 11/10/2004 8.00E-04 -7.13E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #1 7/24/2008 4.80E-03 -5.34E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 7/24/2008 5.90E-03 -5.13E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 6/29/2004 1.86E-02 -3.98E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 11/10/2004 1.40E-03 -6.57E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 11/9/2004 2.30E-03 -6.07E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 8/20/1996 1.15E-02 -4.47E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #2 8/8/2000 2.27E-02 -3.79E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 6/29/2004 3.00E-03 -5.81E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 11/11/2004 4.00E-04 -7.82E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 8/20/1996 5.21E-02 -2.95E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 8/8/2000 1.33E-02 -4.32E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 11/10/2004 1.80E-03 -6.32E+00

YES Coal 7

TNEastman_NO_CBIDATA Boiler 25

Particulate Matter (PM) filterable Sample #3 7/24/2008 8.50E-03 -4.77E+00

YES Coal 8

IAIAStateUnivPowerPlant B1

Particulate Matter (PM) filterable Sample #1 3/26/2008 1.00E-03 -6.91E+00

YES Coal 8

IAIAStateUnivPowerPlant B1

Particulate Matter (PM) filterable Sample #2 3/26/2008 1.00E-03 -6.91E+00

YES Coal 8

IAIAStateUnivPowerPlant B1

Particulate Matter (PM) filterable Sample #3 3/26/2008 1.00E-03 -6.91E+00

YES Coal 9

OHSmartPapersHoldingsLLC B010

Particulate Matter (PM) filterable Sample #1 8/11/2005 1.10E-03 -6.81E+00

YES Coal 9

OHSmartPapersHoldingsLLC B010

Particulate Matter (PM) filterable Sample #2 8/11/2005 5.00E-04 -7.60E+00

YES Coal 9

OHSmartPapersHoldingsLLC B010

Particulate Matter (PM) filterable Sample #3 8/11/2005 1.40E-03 -6.57E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 3/9/2005 1.20E-03 -6.73E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 3/10/2005 2.40E-03 -6.03E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 9/25/1997 1.23E-02 -4.40E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 5/17/2005 3.10E-03 -5.78E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 8/28/2001 1.31E-02 -4.34E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #1 7/12/1993 1.82E-02 -4.01E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 7/12/1993 9.90E-03 -4.62E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 9/25/1997 5.90E-03 -5.13E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 8/28/2001 4.00E-03 -5.52E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 3/9/2005 1.60E-03 -6.44E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 5/17/2005 5.80E-03 -5.15E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #2 3/10/2005 9.30E-04 -6.98E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 3/9/2005 8.00E-04 -7.13E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 5/17/2005 2.70E-03 -5.91E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 9/25/1997 4.02E-03 -5.52E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 7/12/1993 1.52E-02 -4.19E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 3/10/2005 2.20E-03 -6.12E+00

YES Coal 10

TNEastman_NO_CBIDATA Boiler 27

Particulate Matter (PM) filterable Sample #3 8/28/2001 5.00E-03 -5.30E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable 1 9/22/2009 1.28E-03 -6.66E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable 1 9/22/2009 1.28E-03 -6.66E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable 2 9/22/2009 1.54E-03 -6.48E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable 2 8/6/2009 1.19E-03 -6.74E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable 3 9/23/2009 1.25E-03 -6.69E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable 3 8/5/2009 1.68E-03 -6.39E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable Sample #1 9/12/2007 4.60E-03 -5.38E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable Sample #2 9/12/2007 3.00E-03 -5.81E+00

YES Coal 11

WINewPageBiron B24

Particulate Matter (PM) filterable Sample #3 9/12/2007 3.60E-03 -5.63E+00

YES Coal 12

IDTASCONampa Riley Boiler

Particulate Matter (PM) filterable Sample #1 1/12/2004 1.56E-03 -6.46E+00

YES Coal 12

IDTASCONampa Riley Boiler

Particulate Matter (PM) filterable Sample #2 1/12/2004 1.43E-03 -6.55E+00

YES Coal 12

IDTASCONampa Riley Boiler

Particulate Matter (PM) filterable Sample #3 1/12/2004 1.35E-03 -6.61E+00

YES Coal 13

INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #1 4/7/2005 1.50E-03 -6.50E+00

YES Coal 13

INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #1 6/28/2006 1.60E-03 -6.44E+00

YES Coal 13

INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #2 6/28/2006 9.00E-04 -7.01E+00

YES Coal 13

INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #2 4/7/2005 9.00E-04 -7.01E+00

YES Coal 13

INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #3 6/28/2006 3.00E-03 -5.81E+00

YES Coal 13

INSABICInnovativePlastics

01-001 BW1 Boiler

Particulate Matter (PM) filterable Sample #3 4/7/2005 2.20E-03 -6.12E+00

YES Coal 14

INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #1 6/28/2006 1.60E-03 -6.44E+00

YES Coal 14

INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #1 4/7/2005 1.50E-03 -6.50E+00

YES Coal 14

INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #2 6/28/2006 9.00E-04 -7.01E+00

YES Coal 14

INSABICInnovativePlastic

s

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #2 4/7/2005 9.00E-04 -7.01E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 14

INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #3 6/28/2006 3.00E-03 -5.81E+00

YES Coal 14

INSABICInnovativePlastics

01-001 BW2 Boiler

Particulate Matter (PM) filterable Sample #3 4/7/2005 2.20E-03 -6.12E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #1 11/2/2005 1.90E-03 -6.27E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #1 10/31/2005 3.70E-03 -5.60E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #1 11/3/2005 5.40E-02 -2.92E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #2 10/31/2005 2.40E-03 -6.03E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #2 11/2/2005 2.80E-03 -5.88E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #2 11/3/2005 2.71E-02 -3.61E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #3 10/31/2005 5.00E-03 -5.30E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #3 11/2/2005 5.00E-04 -7.60E+00

YES Coal 15

MNAmericanCrystalCrookston Boiler 1

Particulate Matter (PM) filterable Sample #3 11/3/2005 1.76E-02 -4.04E+00

YES Coal 16

IAADMCornProcessingCR EU-502B

Particulate Matter (PM) filterable Sample #1 11/28/1994 1.80E-03 -6.32E+00

YES Coal 16

IAADMCornProcessingCR EU-502B

Particulate Matter (PM) filterable Sample #2 11/28/1994 3.80E-03 -5.57E+00

YES Coal 16

IAADMCornProcessingCR EU-502B

Particulate Matter (PM) filterable Sample #3 11/28/1994 1.00E-03 -6.91E+00

YES Coal 17 WIWausau

# 5 Power Boiler (B24)

Particulate Matter (PM) filterable Sample #1 7/24/2007 ND 1.34E-03 -6.62E+00

YES Coal 17 WIWausau

# 5 Power Boiler (B24)

Particulate Matter (PM) filterable Sample #2 7/24/2007 3.56E-03 -5.64E+00

YES Coal 17 WIWausau

# 5 Power Boiler (B24)

Particulate Matter (PM) filterable Sample #3 7/24/2007 2.02E-03 -6.20E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 18

AKDoyonUtilities_AK 4

Particulate Matter (PM) filterable Sample #1 8/17/2005 2.00E-03 -6.21E+00

YES Coal 18

AKDoyonUtilities_AK 4

Particulate Matter (PM) filterable Sample #2 8/17/2005 2.30E-03 -6.07E+00

YES Coal 18

AKDoyonUtilities_AK 4

Particulate Matter (PM) filterable Sample #3 8/17/2005 2.70E-03 -5.91E+00

YES Coal 19

INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable M5-1 7/21/2009 2.79E-03 -5.88E+00

YES Coal 19

INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable M5-2 7/21/2009 2.82E-03 -5.87E+00

YES Coal 19

INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable M5-3 7/22/2009 2.77E-03 -5.89E+00

YES Coal 19

INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable Sample #1 11/29/2006 5.00E-03 -5.30E+00

YES Coal 19

INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable Sample #2 11/29/2006 1.00E-03 -6.91E+00

YES Coal 19

INPurdueUniverisity Boiler 5

Particulate Matter (PM) filterable Sample #3 11/29/2006 1.00E-03 -6.91E+00

YES Coal 20

VAUniversityofVirginia 7103-1-02R

Particulate Matter (PM) filterable Sample #1 1/16/2007 4.00E-03 -5.52E+00

YES Coal 20

VAUniversityofVirginia 7103-1-02R

Particulate Matter (PM) filterable Sample #2 1/16/2007 1.00E-03 -6.91E+00

YES Coal 20

VAUniversityofVirginia 7103-1-02R

Particulate Matter (PM) filterable Sample #3 1/16/2007 2.00E-03 -6.21E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable 1 8/26/2009 4.65E-03 -5.37E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable 2 8/27/2009 1.73E-03 -6.36E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable 3 8/27/2009 1.42E-03 -6.56E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 11/8/1994 9.10E-03 -4.70E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 9/19/2006 9.90E-03 -4.62E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 9/19/2002 3.00E-03 -5.81E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #1 12/29/1993 2.16E-02 -3.84E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 9/19/2002 ND 2.70E-03 -5.91E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 11/8/1994 6.60E-03 -5.02E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 12/29/1993 1.41E-02 -4.26E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #2 9/19/2006 1.33E-02 -4.32E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 11/8/1994 7.10E-03 -4.95E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 9/19/2002 3.20E-03 -5.74E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 12/29/1993 1.56E-02 -4.16E+00

YES Coal 21

TNEastman_NO_CBIDATA Boiler 30

Particulate Matter (PM) filterable Sample #3 9/19/2006 9.30E-03 -4.68E+00

YES Coal 22

ILRockIslandArsenal

NBN 12602 (Boiler #1)

Particulate Matter (PM) filterable Sample #1 3/13/2007 4.26E-03 -5.46E+00

YES Coal 22

ILRockIslandArsenal

NBN 12602 (Boiler #1)

Particulate Matter (PM) filterable Sample #2 3/13/2007 2.43E-03 -6.02E+00

YES Coal 22

ILRockIslandArsenal

NBN 12602 (Boiler #1)

Particulate Matter (PM) filterable Sample #3 3/13/2007 1.39E-03 -6.58E+00

YES Coal 23

OHUofCincinnati B108

Particulate Matter (PM) filterable Sample #1 4/26/2006 2.90E-03 -5.84E+00

YES Coal 23

OHUofCincinnati B108

Particulate Matter (PM) filterable Sample #2 4/26/2006 3.03E-03 -5.80E+00

YES Coal 23

OHUofCincinnati B108

Particulate Matter (PM) filterable Sample #3 4/27/2005 2.40E-03 -6.03E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/25/2006 3.30E-03 -5.71E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/24/2000 5.90E-02 -2.83E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/19/2004 1.37E-02 -4.29E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #1 10/9/2002 3.60E-02 -3.32E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/24/2000 2.20E-02 -3.82E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/25/2006 4.20E-03 -5.47E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/19/2004 5.10E-03 -5.28E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #2 10/9/2002 4.40E-02 -3.12E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/19/2004 2.80E-03 -5.88E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/9/2002 3.40E-02 -3.38E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/24/2000 4.40E-02 -3.12E+00

YES Coal 24

SCInternationalPaperEastover

No. 1 Power Boiler

Particulate Matter (PM) filterable Sample #3 10/25/2006 1.20E-03 -6.73E+00

YES Coal 25

WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #1 2/22/2006 4.89E-03 -5.32E+00

YES Coal 25

WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #2 2/22/2006 1.58E-03 -6.45E+00

YES Coal 25

WIThilmanyPapersNicoletMill B23

Particulate Matter (PM) filterable Sample #3 2/22/2006 2.34E-03 -6.06E+00

YES Coal 26

WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #1 2/22/2006 4.89E-03 -5.32E+00

YES Coal 26

WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #2 2/22/2006 1.58E-03 -6.45E+00

YES Coal 26

WIThilmanyPapersNicoletMill B24

Particulate Matter (PM) filterable Sample #3 2/22/2006 2.34E-03 -6.06E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 27

IDAmalgamatedSugarCoTwinFalls S-B1

Particulate Matter (PM) filterable Sample #1 9/26/2006 2.01E-03 -6.21E+00

YES Coal 27

IDAmalgamatedSugarCoTwinFalls S-B1

Particulate Matter (PM) filterable Sample #2 9/26/2006 3.26E-03 -5.72E+00

YES Coal 27

IDAmalgamatedSugarCoTwinFalls S-B1

Particulate Matter (PM) filterable Sample #3 9/26/2006 4.10E-03 -5.50E+00

YES Coal 28 ILPolyOne B1

Particulate Matter (PM) filterable 1 9/9/2009 4.59E-03 -5.38E+00

YES Coal 28 ILPolyOne B1

Particulate Matter (PM) filterable 2 9/9/2009 5.32E-03 -5.24E+00

YES Coal 28 ILPolyOne B1

Particulate Matter (PM) filterable 3 9/10/2009 1.26E-02 -4.37E+00

YES Coal 28 ILPolyOne B1

Particulate Matter (PM) filterable Sample #1 11/14/2006 3.20E-03 -5.74E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 8/14/2006 4.21E-02 -3.17E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 8/4/1994 3.30E-03 -5.71E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 12/14/1994 9.10E-03 -4.70E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 12/6/2006 4.50E-03 -5.40E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 9/29/1998 1.24E-02 -4.39E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 9/17/2002 8.30E-03 -4.79E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 3/15/2005 5.00E-03 -5.30E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #1 7/25/2006 6.19E-02 -2.78E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 12/6/2006 2.70E-03 -5.91E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 9/17/2002 7.00E-03 -4.96E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 12/15/1994 2.80E-03 -5.88E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 3/15/2005 5.00E-03 -5.30E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 8/4/1994 2.90E-03 -5.84E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 7/25/2006 2.20E-02 -3.82E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 8/14/2006 4.59E-02 -3.08E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #2 9/29/1998 6.51E-03 -5.03E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 12/6/2006 3.20E-03 -5.74E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 7/25/2006 4.15E-02 -3.18E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 8/14/2006 5.45E-02 -2.91E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 8/4/1994 4.50E-03 -5.40E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 12/15/1994 6.70E-03 -5.01E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 3/15/2005 4.80E-03 -5.34E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 9/17/2002 4.90E-03 -5.32E+00

YES Coal 29

TNEastman_NO_CBIDATA Boiler 31

Particulate Matter (PM) filterable Sample #3 9/29/1998 9.68E-03 -4.64E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable 1 8/4/2009 4.18E-03 -5.48E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable 2 8/5/2009 3.30E-03 -5.71E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable 3 8/5/2009 3.11E-03 -5.77E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #1 2/15/2006 5.40E-03 -5.22E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #1 2/22/2006 4.10E-03 -5.50E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #2 2/21/2006 6.60E-03 -5.02E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #2 2/23/2006 3.20E-03 -5.74E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #3 2/21/2006 7.00E-03 -4.96E+00

YES Coal 30 IAUofIowa

EP7 Boiler 11

Particulate Matter (PM) filterable Sample #3 2/23/2006 3.80E-03 -5.57E+00

YES Coal 31

ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable OTM28-1 8/4/2009 3.89E-03 -5.55E+00

YES Coal 31

ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable OTM28-2 8/5/2009 3.06E-03 -5.79E+00

YES Coal 31

ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable OTM28-3 8/5/2009 3.82E-03 -5.57E+00

YES Coal 31

ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable Sample #1 8/22/2007 2.10E-02 -3.86E+00

YES Coal 31

ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable Sample #2 8/22/2007 2.30E-02 -3.77E+00

YES Coal 31

ILAbbottAbbottPark Unit 5AP

Particulate Matter (PM) filterable Sample #3 8/22/2007 1.90E-02 -3.96E+00

YES Coal 32

VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #1 10/12/2004 4.00E-03 -5.52E+00

YES Coal 32

VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #1 10/12/2004 2.40E-02 -3.73E+00

YES Coal 32

VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #2 10/12/2004 1.20E-02 -4.42E+00

YES Coal 32

VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #2 10/12/2004 3.00E-03 -5.81E+00

YES Coal 32

VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #3 10/12/2004 4.00E-03 -5.52E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 32

VADukeEnergyNarrows Boiler #2

Particulate Matter (PM) filterable Sample #3 10/12/2004 1.00E-02 -4.61E+00

YES Coal 33

OHSmartPapersHoldingsLLC B020

Particulate Matter (PM) filterable Sample #1 9/22/2005 6.50E-03 -5.04E+00

YES Coal 33

OHSmartPapersHoldingsLLC B020

Particulate Matter (PM) filterable Sample #2 9/22/2005 5.00E-04 -7.60E+00

YES Coal 33

OHSmartPapersHoldingsLLC B020

Particulate Matter (PM) filterable Sample #3 9/22/2005 4.20E-03 -5.47E+00

YES Coal 34

AKDoyonUtilities_AK 7

Particulate Matter (PM) filterable Sample #1 8/16/2005 3.30E-03 -5.71E+00

YES Coal 34

AKDoyonUtilities_AK 7

Particulate Matter (PM) filterable Sample #2 8/16/2005 4.20E-03 -5.47E+00

YES Coal 34

AKDoyonUtilities_AK 7

Particulate Matter (PM) filterable Sample #3 8/16/2005 4.00E-03 -5.52E+00

YES Coal 35

VAGPBigIsland2703

PWR04 - No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #1 5/1/2007 4.40E-03 -5.43E+00

YES Coal 35

VAGPBigIsland2703

PWR04 - No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #2 5/1/2007 3.80E-03 -5.57E+00

YES Coal 35

VAGPBigIsland2703

PWR04 - No. 4 Power Boiler

Particulate Matter (PM) filterable Sample #3 5/1/2007 3.80E-03 -5.57E+00

YES Coal 36

VAUniversityofVirginia 7103-1-05

Particulate Matter (PM) filterable Sample #1 4/4/2008 1.80E-03 -6.32E+00

YES Coal 36

VAUniversityofVirginia 7103-1-05

Particulate Matter (PM) filterable Sample #2 4/4/2008 1.80E-03 -6.32E+00

YES Coal 36

VAUniversityofVirginia 7103-1-05

Particulate Matter (PM) filterable Sample #3 4/4/2008 9.00E-03 -4.71E+00

YES Coal 37

VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #1 10/14/2004 2.00E-03 -6.21E+00

YES Coal 37

VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #1 4/14/2004 4.80E-02 -3.04E+00

YES Coal 37

VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #2 4/14/2004 2.60E-02 -3.65E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Coal 37

VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #2 10/14/2004 4.00E-03 -5.52E+00

YES Coal 37

VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #3 10/14/2004 7.00E-03 -4.96E+00

YES Coal 37

VADukeEnergyNarrows Boiler #3

Particulate Matter (PM) filterable Sample #3 4/14/2004 2.90E-02 -3.54E+00

YES Coal 38 INNotreDame B-4

Particulate Matter (PM) filterable Sample #1 8/26/2009 4.00E-03 -5.52E+00

YES Coal 38 INNotreDame B-4

Particulate Matter (PM) filterable Sample #1 2/21/2006 1.56E-01 -1.86E+00

YES Coal 38 INNotreDame B-4

Particulate Matter (PM) filterable Sample #2 8/26/2009 5.20E-03 -5.26E+00

YES Coal 38 INNotreDame B-4

Particulate Matter (PM) filterable Sample #2 2/21/2006 1.05E-01 -2.26E+00

YES Coal 38 INNotreDame B-4

Particulate Matter (PM) filterable Sample #3 8/27/2009 4.30E-03 -5.45E+00

YES Coal 39

NCHanesDyeWinstonSalem ES B01

Particulate Matter (PM) filterable Sample #1 3/21/2007 6.40E-03 -5.05E+00

YES Coal 39

NCHanesDyeWinstonSalem ES B01

Particulate Matter (PM) filterable Sample #2 3/21/2007 2.80E-03 -5.88E+00

YES Coal 39

NCHanesDyeWinstonSalem ES B01

Particulate Matter (PM) filterable Sample #3 3/21/2007 4.70E-03 -5.36E+00

YES Coal 40

NCHanesDyeWinstonSalem ES B02

Particulate Matter (PM) filterable Sample #1 3/21/2007 6.40E-03 -5.05E+00

YES Coal 40

NCHanesDyeWinstonSalem ES B02

Particulate Matter (PM) filterable Sample #2 3/21/2007 2.80E-03 -5.88E+00

YES Coal 40

NCHanesDyeWinstonSalem ES B02

Particulate Matter (PM) filterable Sample #3 3/21/2007 4.70E-03 -5.36E+00

YES Coal 41

OKGPMuskogeeMill B-3

Particulate Matter (PM) filterable Sample #1 5/20/2003 7.00E-03 -4.96E+00

YES Coal 41

OKGPMuskogeeMill B-3

Particulate Matter (PM) filterable Sample #2 5/20/2003 5.00E-03 -5.30E+00

YES Coal 41

OKGPMuskogeeMill B-3

Particulate Matter (PM) filterable Sample #3 5/20/2003 2.00E-03 -6.21E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 1 1

IAADMClinton

EUCOG-5 #2 Gas Fired Boiler

Particulate Matter (PM) filterable Sample #1 3/5/2008 1.00E-04 -9.21E+00

YES Gas 1 1

IAADMClinton

EUCOG-5 #2 Gas Fired Boiler

Particulate Matter (PM) filterable Sample #2 3/7/2008 2.00E-04 -8.52E+00

YES Gas 1 1

IAADMClinton

EUCOG-5 #2 Gas Fired Boiler

Particulate Matter (PM) filterable Sample #3 3/10/2008 1.00E-04 -9.21E+00

YES Gas 1 2

MSChevronPascagoula F-2103

Particulate Matter (PM) filterable Sample #1 3/27/2008 1.20E-04 -9.03E+00

YES Gas 1 2

MSChevronPascagoula F-2103

Particulate Matter (PM) filterable Sample #2 3/27/2008 1.20E-04 -9.03E+00

YES Gas 1 2

MSChevronPascagoula F-2103

Particulate Matter (PM) filterable Sample #3 3/27/2008 5.60E-04 -7.49E+00

YES Gas 1 3

IACargillEddyville 84.000

Particulate Matter (PM) filterable Sample #1 11/25/1997 3.14E-04 -8.06E+00

YES Gas 1 3

IACargillEddyville 84.000

Particulate Matter (PM) filterable Sample #2 11/25/1997 2.83E-04 -8.17E+00

YES Gas 1 3

IACargillEddyville 84.000

Particulate Matter (PM) filterable Sample #3 11/25/1997 2.52E-04 -8.29E+00

YES Gas 1 4

IACargillEddyville 86.000

Particulate Matter (PM) filterable Sample #1 11/25/1997 3.14E-04 -8.06E+00

YES Gas 1 4

IACargillEddyville 86.000

Particulate Matter (PM) filterable Sample #2 11/25/1997 2.83E-04 -8.17E+00

YES Gas 1 4

IACargillEddyville 86.000

Particulate Matter (PM) filterable Sample #3 11/25/1997 2.52E-04 -8.29E+00

YES Gas 1 5

MABostonGeneratingMysticStation EU-17

Particulate Matter (PM) filterable Sample #1 8/14/2008 4.00E-04 -7.82E+00

YES Gas 1 5

MABostonGeneratingMysticStation EU-17

Particulate Matter (PM) filterable Sample #2 8/14/2008 4.00E-04 -7.82E+00

YES Gas 1 5

MABostonGeneratingMysticStation EU-17

Particulate Matter (PM) filterable Sample #3 8/14/2008 1.00E-04 -9.21E+00

YES Gas 1 6

MSDuPontDeLisle1342

AH-202 (BLR1342)

Particulate Matter (PM) filterable Sample #1 3/29/2007 3.76E-04 -7.89E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 1 6

MSDuPontDeLisle1342

AH-202 (BLR1342)

Particulate Matter (PM) filterable Sample #2 3/29/2007 2.27E-04 -8.39E+00

YES Gas 1 6

MSDuPontDeLisle1342

AH-202 (BLR1342)

Particulate Matter (PM) filterable Sample #3 3/29/2007 3.45E-04 -7.97E+00

YES Gas 1 7

IAKochNitrogen

ReformerAux Boiler

Particulate Matter (PM) filterable Sample #1 1/4/2007 6.17E-04 -7.39E+00

YES Gas 1 7

IAKochNitrogen

ReformerAux Boiler

Particulate Matter (PM) filterable Sample #2 1/4/2007 2.03E-04 -8.50E+00

YES Gas 1 7

IAKochNitrogen

ReformerAux Boiler

Particulate Matter (PM) filterable Sample #3 1/5/2007 2.55E-04 -8.27E+00

YES Gas 1 8

NCCampLejeuneMCB

C-AS-4151-16

Particulate Matter (PM) filterable Sample #1 9/30/2009 3.10E-04 -8.08E+00

YES Gas 1 8

NCCampLejeuneMCB

C-AS-4151-16

Particulate Matter (PM) filterable Sample #2 10/1/2009 4.40E-04 -7.73E+00

YES Gas 1 8

NCCampLejeuneMCB

C-AS-4151-16

Particulate Matter (PM) filterable Sample #3 10/1/2009 5.10E-04 -7.58E+00

YES Gas 1 9

IAGrainProcessing Boiler #10

Particulate Matter (PM) filterable Sample #1 7/24/2007 5.73E-04 -7.47E+00

YES Gas 1 9

IAGrainProcessing Boiler #10

Particulate Matter (PM) filterable Sample #2 7/24/2007 5.73E-04 -7.47E+00

YES Gas 1 9

IAGrainProcessing Boiler #10

Particulate Matter (PM) filterable Sample #3 7/24/2007 1.43E-04 -8.85E+00

YES Gas 1 10

TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #1 6/11/2003 6.00E-04 -7.42E+00

YES Gas 1 10

TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #2 6/11/2003 4.00E-04 -7.82E+00

YES Gas 1 10

TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #3 6/11/2003 3.00E-04 -8.11E+00

YES Gas 1 10

TNValeroMemphis

P021 - No. 10 Boiler

Particulate Matter (PM) filterable Sample #3 12/11/2002 7.00E-04 -7.26E+00

YES Gas 1 11

MSChevronPascagoula F-8510

Particulate Matter (PM) filterable Sample #1 11/6/2007 4.44E-04 -7.72E+00

YES Gas 1 11

MSChevronPascagoula F-8510

Particulate Matter (PM) filterable Sample #2 11/6/2007 2.22E-04 -8.41E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 1 11

MSChevronPascagoula F-8510

Particulate Matter (PM) filterable Sample #3 11/6/2007 6.38E-04 -7.36E+00

YES Gas 1 12

MSDuPontDeLisle1342

AH-101 (BLR1342)

Particulate Matter (PM) filterable Sample #1 3/14/2008 5.72E-04 -7.47E+00

YES Gas 1 12

MSDuPontDeLisle1342

AH-101 (BLR1342)

Particulate Matter (PM) filterable Sample #2 3/14/2008 4.15E-04 -7.79E+00

YES Gas 1 12

MSDuPontDeLisle1342

AH-101 (BLR1342)

Particulate Matter (PM) filterable Sample #3 3/14/2008 3.61E-04 -7.93E+00

YES Gas 1 13

MDUofMaryland EU 001-4

Particulate Matter (PM) filterable Sample #1 2/20/2002 4.98E-04 -7.60E+00

YES Gas 1 13

MDUofMaryland EU 001-4

Particulate Matter (PM) filterable Sample #2 2/20/2002 3.98E-04 -7.83E+00

YES Gas 1 13

MDUofMaryland EU 001-4

Particulate Matter (PM) filterable Sample #3 2/20/2002 5.98E-04 -7.42E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #1 2/28/2007 2.89E-02 -3.54E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #1 5/17/2007 1.00E-03 -6.91E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #1 5/15/2007 6.00E-04 -7.42E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #2 5/17/2007 1.00E-04 -9.21E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #2 2/28/2007 3.16E-02 -3.45E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #2 5/15/2007 3.10E-03 -5.78E+00

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #3 5/15/2007 2.00E-04 -8.52E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 1 14

TNValeroMemphis

P044-DHT 18 Stripper Reboiler Heater

Particulate Matter (PM) filterable Sample #3 2/28/2007 2.81E-02 -3.57E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #1 5/16/2007 1.50E-03 -6.50E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #1 2/27/2007 1.08E-01 -2.23E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #1 5/15/2007 1.60E-03 -6.44E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #2 2/27/2007 1.20E-02 -4.42E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #2 5/15/2007 2.30E-03 -6.07E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #2 5/16/2007 1.00E-04 -9.21E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #3 5/16/2007 1.00E-04 -9.21E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #3 2/27/2007 1.24E-02 -4.39E+00

YES Gas 1 15

TNValeroMemphis

P043 - DHT 18 Reactor Feed Heater

Particulate Matter (PM) filterable Sample #3 5/15/2007 4.80E-03 -5.34E+00

YES Gas 1 16

NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #1 10/11/2007 1.00E-03 -6.91E+00

YES Gas 1 16

NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #2 10/11/2007 3.00E-04 -8.11E+00

YES Gas 1 16

NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #3 10/11/2007 5.00E-04 -7.60E+00

YES Gas 1 17

NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #1 11/14/2007 4.81E-04 -7.64E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 1 17

NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #2 11/14/2007 4.36E-04 -7.74E+00

YES Gas 1 17

NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #3 11/14/2007 9.50E-04 -6.96E+00

YES Gas 1 18

NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #1 8/27/2008 9.21E-04 -6.99E+00

YES Gas 1 18

NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #2 8/28/2008 7.00E-04 -7.26E+00

YES Gas 1 18

NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #3 8/28/2008 2.48E-04 -8.30E+00

YES Gas 1 yes 1

INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable 1 9/25/2009 5.24E-06 -1.22E+01

YES Gas 1 yes 1

INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable 2 9/26/2009 3.73E-06 -1.25E+01

YES Gas 1 yes 1

INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable 3 9/26/2009 5.39E-06 -1.21E+01

YES Gas 1 yes 1

INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable Sample #1 9/19/1997 1.40E-02 -4.27E+00

YES Gas 1 yes 1

INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable Sample #2 9/19/1997 9.90E-03 -4.62E+00

YES Gas 1 yes 1

INArcelorMittalBurnsHarbor

Hot Dip Coating Line Annealing Furnace

Particulate Matter (PM) filterable Sample #3 9/19/1997 1.53E-02 -4.18E+00

YES Gas 1 yes 2 INNucorSteel

Cold Mill Annealing

Particulate Matter (PM) filterable M5-1 8/18/2009 1.39E-03 -6.58E+00

YES Gas 1 yes 2 INNucorSteel

Cold Mill Annealing

Particulate Matter (PM) filterable M5-2 8/18/2009 7.90E-04 -7.14E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 1 yes 2 INNucorSteel

Cold Mill Annealing

Particulate Matter (PM) filterable M5-3 8/18/2009 9.28E-04 -6.98E+00

YES Gas 2 1

LAShellChemicaGeismar

Furnace FS801

Particulate Matter (PM) filterable 528-1 8/26/2009 8.21E-04 -7.10E+00

YES Gas 2 1

LAShellChemicaGeismar

Furnace FS801

Particulate Matter (PM) filterable 528-2 8/26/2009 2.33E-04 -8.36E+00

YES Gas 2 1

LAShellChemicaGeismar

Furnace FS801

Particulate Matter (PM) filterable 528-3 8/27/2009 2.06E-04 -8.49E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 8/29/2000 8.10E-03 -4.82E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 9/21/2007 5.50E-04 -7.51E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 8/10/2004 2.61E-02 -3.65E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 7/28/1998 6.00E-03 -5.12E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 11/9/1999 2.65E-02 -3.63E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 2/2/2000 3.18E-03 -5.75E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 10/27/1992 1.00E-02 -4.61E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 9/24/1994 1.44E-02 -4.24E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 8/28/2002 7.20E-03 -4.93E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #1 7/19/2000 3.10E-03 -5.78E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 8/29/2000 2.12E-02 -3.85E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 2/2/2000 3.92E-03 -5.54E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 9/21/2007 1.06E-03 -6.85E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 8/10/2004 3.76E-02 -3.28E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 9/24/1994 1.21E-02 -4.41E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 8/28/2002 6.70E-03 -5.01E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 10/27/1992 1.30E-02 -4.34E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 11/9/1999 2.11E-02 -3.86E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 7/28/1998 1.60E-03 -6.44E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #2 7/19/2000 2.70E-03 -5.91E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 10/27/1992 1.30E-02 -4.34E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 9/24/1994 2.94E-02 -3.53E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 8/29/2000 1.40E-03 -6.57E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 7/19/2000 7.00E-03 -4.96E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 9/21/2007 7.60E-04 -7.18E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 7/28/1998 2.40E-03 -6.03E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 8/10/2004 4.21E-02 -3.17E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 11/9/1999 2.56E-02 -3.67E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 8/28/2002 1.02E-02 -4.59E+00

YES Gas 2 2

WIGPGreenBay2818

B29 - Fluidized Bed Boiler #9

Particulate Matter (PM) filterable Sample #3 2/2/2000 3.92E-03 -5.54E+00

YES Liquid 1

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86

Particulate Matter (PM) filterable 1 11/17/2009 7.19E-04 -7.24E+00

YES Liquid 1

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86

Particulate Matter (PM) filterable 2 11/17/2009 4.12E-04 -7.80E+00

YES Liquid 1

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86

Particulate Matter (PM) filterable 3 11/18/2009 DLL 4.02E-04 -7.82E+00

YES Liquid 2

SCGPChemRussellville FO Boiler

Particulate Matter (PM) filterable Sample #1 8/26/2009 8.00E-04 -7.13E+00

YES Liquid 2

SCGPChemRussellville FO Boiler

Particulate Matter (PM) filterable Sample #2 8/26/2009 5.00E-04 -7.60E+00

YES Liquid 2

SCGPChemRussellville FO Boiler

Particulate Matter (PM) filterable Sample #3 8/26/2009 5.00E-04 -7.60E+00

YES Liquid 3

NJSunocoWestville Boiler #8

Particulate Matter (PM) filterable Sample #1 11/20/2007 9.34E-04 -6.98E+00

YES Liquid 3

NJSunocoWestville Boiler #8

Particulate Matter (PM) filterable Sample #2 11/20/2007 8.82E-05 -9.34E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Liquid 3

NJSunocoWestville Boiler #8

Particulate Matter (PM) filterable Sample #3 11/20/2007 1.01E-03 -6.90E+00

YES Liquid 4

PAConemaughPowerPlantNewFlorence Aux Boiler B

Particulate Matter (PM) filterable Sample #1 10/17/2006 1.30E-03 -6.65E+00

YES Liquid 4

PAConemaughPowerPlantNewFlorence Aux Boiler B

Particulate Matter (PM) filterable Sample #2 10/17/2006 3.20E-04 -8.05E+00

YES Liquid 4

PAConemaughPowerPlantNewFlorence Aux Boiler B

Particulate Matter (PM) filterable Sample #3 10/17/2006 1.00E-03 -6.91E+00

YES Liquid 5

NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #1 11/15/2007 8.01E-04 -7.13E+00

YES Liquid 5

NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #2 11/15/2007 9.65E-04 -6.94E+00

YES Liquid 5

NJSunocoWestville Boiler #6

Particulate Matter (PM) filterable Sample #3 11/15/2007 1.30E-03 -6.65E+00

YES Liquid 6

PACherokeePharm

SG-C, Title V Source ID 037

Particulate Matter (PM) filterable Sample #1 5/21/1998 2.00E-03 -6.21E+00

YES Liquid 6

PACherokeePharm

SG-C, Title V Source ID 037

Particulate Matter (PM) filterable Sample #2 5/21/1998 1.30E-03 -6.65E+00

YES Liquid 6

PACherokeePharm

SG-C, Title V Source ID 037

Particulate Matter (PM) filterable Sample #3 5/21/1998 1.50E-03 -6.50E+00

YES Liquid 7

NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #1 12/19/2005 1.95E-03 -6.24E+00

YES Liquid 7

NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #2 12/19/2005 2.07E-03 -6.18E+00

YES Liquid 7

NJSunocoWestville Boiler #7

Particulate Matter (PM) filterable Sample #3 12/19/2005 1.13E-03 -6.79E+00

YES Liquid 8

PACherokeePharm

SG-B, Title V Source ID 036

Particulate Matter (PM) filterable Sample #1 5/19/1998 2.20E-03 -6.12E+00

YES Liquid 8

PACherokeePharm

SG-B, Title V Source ID 036

Particulate Matter (PM) filterable Sample #2 5/19/1998 2.00E-03 -6.21E+00

YES Liquid 8

PACherokeePharm

SG-B, Title V Source ID 036

Particulate Matter (PM) filterable Sample #3 5/19/1998 1.20E-03 -6.73E+00
Appendix G-8: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data 

in Top 

12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmBtu ln ( lb/mmBtu)

YES Liquid 9

NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #1 11/16/2007 2.08E-03 -6.18E+00

YES Liquid 9

NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #2 11/16/2007 1.23E-03 -6.70E+00

YES Liquid 9

NJSunocoWestville Boiler #5

Particulate Matter (PM) filterable Sample #3 11/16/2007 2.15E-03 -6.14E+00

YES Liquid 10

ALBPDecatur24 AB-8301

Particulate Matter (PM) filterable Sample #1 1/24/2001 4.51E-03 -5.40E+00

YES Liquid 10

ALBPDecatur24 AB-8301

Particulate Matter (PM) filterable Sample #2 1/24/2001 9.91E-04 -6.92E+00

YES Liquid 10

ALBPDecatur24 AB-8301

Particulate Matter (PM) filterable Sample #3 1/24/2001 1.40E-03 -6.57E+00
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Biomass 1

FLUSSugarCorp Boiler No. 7 Mercury (Hg) Sample #1 1/2/2003 ND 1

YES Biomass 1

FLUSSugarCorp Boiler No. 7 Mercury (Hg) Sample #2 1/2/2003 ND 9

YES Biomass 1

FLUSSugarCorp Boiler No. 7 Mercury (Hg) Sample #3 1/2/2003 ND 8

YES Biomass 2

FLSmurfitStone 5PB Mercury (Hg) Sample #1 7/10/2007 2

YES Biomass 2

FLSmurfitStone 5PB Mercury (Hg) Sample #3 7/10/2007 1

YES Biomass 3

NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #1 9/16/1999 ND 2

YES Biomass 3

NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #1 9/15/1999 ND 2

YES Biomass 3

NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #2 9/20/1999 ND 2

YES Biomass 3

NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #2 9/15/1999 ND 2

YES Biomass 3

NYIntlPaperTiconderoga PB1 Mercury (Hg) Sample #3 9/16/1999 ND 2

YES Biomass 4

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) 1 8/26/2009 DLL 5

YES Biomass 4

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) 2 8/26/2009 DLL 4

YES Biomass 4

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) 3 8/27/2009 DLL 5
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Biomass 4

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) Sample #1 8/3/2005 2

YES Biomass 4

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) Sample #2 8/3/2005 2

YES Biomass 4

NDCargillWestFargo

Foster Wheeler Boiler (EU43) Mercury (Hg) Sample #3 8/3/2005 2

YES Biomass 5

NCGPRoxboro

ES-1 Wood fired Boiler Mercury (Hg) Sample #1 7/14/2004 3

YES Biomass 5

NCGPRoxboro

ES-1 Wood fired Boiler Mercury (Hg) Sample #2 7/14/2004 2

YES Biomass 5

NCGPRoxboro

ES-1 Wood fired Boiler Mercury (Hg) Sample #3 7/14/2004 2

YES Biomass 6

FLSugarCaneGrowersCoop Boiler No. 8 Mercury (Hg) Sample #1 12/16/2002 5

YES Biomass 6

FLSugarCaneGrowersCoop Boiler No. 8 Mercury (Hg) Sample #2 12/16/2002 1

YES Biomass 6

FLSugarCaneGrowersCoop Boiler No. 8 Mercury (Hg) Sample #3 12/16/2002 3

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) 1 8/4/2009 DLL 6

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) 2 8/5/2009 DLL 5

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) 3 8/5/2009 DLL 5

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #1 2/15/2006 1

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #1 2/22/2006 3

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #2 2/23/2006 3
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #2 2/21/2006 ND 7

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #3 2/21/2006 2

YES Coal 1 IAUofIowa

EP7 Boiler 11 Mercury (Hg) Sample #3 2/23/2006 1

YES Coal 2

MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #1 1/9/2007 ND 3

YES Coal 2

MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #1 1/10/2007 ND 3

YES Coal 2

MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #2 1/9/2007 ND 3

YES Coal 2

MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #2 1/10/2007 ND 3

YES Coal 2

MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #3 1/10/2007 ND 3

YES Coal 2

MITBSimonPowerPlant Unit 4 Mercury (Hg) Sample #3 1/9/2007 ND 1

YES Coal 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Mercury (Hg) Sample #1 8/26/2009 ND 3

YES Coal 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Mercury (Hg) Sample #2 8/26/2009 ND 2

YES Coal 3

IAArchersDanielsMidlandDesMoines

Asea Boiler #1 Mercury (Hg) Sample #3 8/27/2009 5

YES Coal 4

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Mercury (Hg) 1 6/3/2009 6

YES Coal 4

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Mercury (Hg) 2 6/3/2009 4
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 4

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121) Mercury (Hg) 3 6/4/2009 8

YES Coal 5

INPurdueUniverisity Boiler 5 Mercury (Hg) M5-1 7/21/2009 1

YES Coal 5

INPurdueUniverisity Boiler 5 Mercury (Hg) M5-2 7/21/2009 1

YES Coal 5

INPurdueUniverisity Boiler 5 Mercury (Hg) M5-3 7/22/2009 1

YES Coal 6 ILPolyOne B1 Mercury (Hg) 1 9/9/2009 1YES Coal 6 ILPolyOne B1 Mercury (Hg) 2 9/9/2009 1YES Coal 6 ILPolyOne B1 Mercury (Hg) 3 9/10/2009 6YES Coal 6 ILPolyOne B1 Mercury (Hg) Sample #1 11/14/2006 2YES Coal 7

MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #1 7/26/2007 ND 3

YES Coal 7

MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #1 7/25/2007 ND 1

YES Coal 7

MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #2 7/26/2007 ND 1

YES Coal 7

MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #2 7/25/2007 ND 9

YES Coal 7

MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #3 7/26/2007 ND 3

YES Coal 7

MITBSimonPowerPlant Unit 2 Mercury (Hg) Sample #3 7/25/2007 ND 1

YES Coal 8

MNADMCornDivision

Coal Boiler #1 EU049 Mercury (Hg) Sample #2 10/25/2008 1

YES Coal 9

MNADMCornDivision

Coal Boiler #2 EU050 Mercury (Hg) Sample #2 10/25/2008 1

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) 1 7/22/2009 DLL 2

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) 2 7/22/2009 DLL 1

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) 3 7/23/2009 DLL 1
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #1 6/13/2007 ND 7

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #1 6/14/2007 ND 1

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #2 6/13/2007 ND 2

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #2 6/14/2007 ND 6

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #3 6/15/2007 1

YES Coal 10

MITBSimonPowerPlant Unit 1 Mercury (Hg) Sample #3 6/14/2007 ND 9

YES Coal 11

NCTysonHarmony TYS-ES-21 Mercury (Hg) Sample #1 9/25/2006 2

YES Coal 11

NCTysonHarmony TYS-ES-21 Mercury (Hg) Sample #2 9/26/2006 2

YES Coal 11

NCTysonHarmony TYS-ES-21 Mercury (Hg) Sample #3 9/27/2006 2

YES Coal 12

IDAmalgamatedSugarCoTwinFalls S-B1 Mercury (Hg) Sample #1 9/26/2006 2

YES Coal 12

IDAmalgamatedSugarCoTwinFalls S-B1 Mercury (Hg) Sample #2 9/26/2006 2

YES Coal 12

IDAmalgamatedSugarCoTwinFalls S-B1 Mercury (Hg) Sample #3 9/26/2006 2

YES Coal 13

AKDoyonUtilities_AK 4 Mercury (Hg) Sample #1 8/17/2005 3

YES Coal 13

AKDoyonUtilities_AK 4 Mercury (Hg) Sample #2 8/17/2005 4

YES Coal 13

AKDoyonUtilities_AK 4 Mercury (Hg) Sample #3 8/17/2005 3

YES Coal 14

IAADMCornProcessingCR EU-501B Mercury (Hg) Sample #1 8/12/2009 8

YES Coal 14

IAADMCornProcessingCR EU-501B Mercury (Hg) Sample #2 8/13/2009 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 14

IAADMCornProcessingCR EU-501B Mercury (Hg) Sample #3 8/13/2009 6

YES Coal 15

VAUniversityofVirginia 7103-1-01R Mercury (Hg) M29-1 9/17/2009 < 3

YES Coal 15

VAUniversityofVirginia 7103-1-01R Mercury (Hg) M29-2 9/17/2009 < 3

YES Coal 15

VAUniversityofVirginia 7103-1-01R Mercury (Hg) M29-3 9/18/2009 < 3

YES Coal 16

VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #1 5/25/2005 5

YES Coal 16

VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #1 11/23/2004 ND 6

YES Coal 16

VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #2 11/24/2004 2

YES Coal 16

VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #2 5/25/2005 4

YES Coal 16

VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #3 11/24/2004 2

YES Coal 16

VADukeEnergyNarrows Boiler #1 Mercury (Hg) Sample #3 5/25/2005 4

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #1 7/25/2006 4

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #1 8/1/2006 1

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #1 8/2/2006 1

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #2 8/2/2006 9

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #2 7/25/2006 4

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #2 8/1/2006 8
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #3 8/2/2006 1

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #3 7/25/2006 3

YES Coal 17

MINeenahPaperMI Boiler 1 Mercury (Hg) Sample #3 8/1/2006 1

YES Coal 18

OHAppletonIdeas

Boiler 4 (B003) Mercury (Hg) Sample #1 1/31/2003 3

YES Coal 18

OHAppletonIdeas

Boiler 4 (B003) Mercury (Hg) Sample #2 1/31/2003 4

YES Coal 18

OHAppletonIdeas

Boiler 4 (B003) Mercury (Hg) Sample #3 1/31/2003 4

YES Coal 19

TNNissanSmyrna Boiler 3 Mercury (Hg) Sample #1 3/3/2007 5

YES Coal 19

TNNissanSmyrna Boiler 3 Mercury (Hg) Sample #2 3/3/2007 3

YES Coal 19

TNNissanSmyrna Boiler 3 Mercury (Hg) Sample #3 3/3/2007 4

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) M5/29-1BH 8/10/2009 < 6

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) M5/29-1FH 8/10/2009 < 5

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) M5/29-2BH 8/11/2009 < 8

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) M5/29-2FH 8/11/2009 < 8

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) M5/29-3BH 8/11/2009 < 8

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) M5/29-3FH 8/11/2009 < 8

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) Sample #1 11/25/2003 ND 1

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) Sample #2 11/25/2003 ND 1

YES Coal 20

NCUNCCogen ES-001 Mercury (Hg) Sample #3 11/25/2003 ND 1

YES Coal 21

INTateLyleSagamore 31B1 Mercury (Hg) M29-1 9/1/2009 4

YES Coal 21

INTateLyleSagamore 31B1 Mercury (Hg) M29-2 9/2/2009 4
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 21

INTateLyleSagamore 31B1 Mercury (Hg) M29-3 9/3/2009 4

YES Coal 22

OKGPMuskogeeMill B-3 Mercury (Hg) Sample #1 5/20/2003 4

YES Coal 22

OKGPMuskogeeMill B-3 Mercury (Hg) Sample #2 5/20/2003 4

YES Coal 22

OKGPMuskogeeMill B-3 Mercury (Hg) Sample #3 5/20/2003 6

YES Coal 23

TNCargillMemphis

Stoker Boiler 8001 Mercury (Hg) 1 8/5/2009 DLL 4

YES Coal 23

TNCargillMemphis

Stoker Boiler 8001 Mercury (Hg) 2 11/6/2009 DLL 5

YES Coal 23

TNCargillMemphis

Stoker Boiler 8001 Mercury (Hg) 3 8/6/2009 DLL 4

YES Coal 24

WIWausauRhine B26 Mercury (Hg) Sample #1 9/5/2007 7

YES Coal 24

WIWausauRhine B26 Mercury (Hg) Sample #2 9/5/2007 3

YES Coal 24

WIWausauRhine B26 Mercury (Hg) Sample #3 9/5/2007 3

YES Coal 25

ALIPCourtland

No.2 Combination Boiler / 11CU201 Mercury (Hg) Sample #1 9/10/1996 5

YES Coal 25

ALIPCourtland

No.2 Combination Boiler / 11CU201 Mercury (Hg) Sample #2 9/10/1996 4

YES Coal 25

ALIPCourtland

No.2 Combination Boiler / 11CU201 Mercury (Hg) Sample #3 9/10/1996 5

YES Coal 26

VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #1 10/12/2004 7

YES Coal 26

VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #1 10/12/2004 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 26

VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #2 10/12/2004 4

YES Coal 26

VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #2 10/12/2004 1

YES Coal 26

VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #3 10/12/2004 3

YES Coal 26

VADukeEnergyNarrows Boiler #2 Mercury (Hg) Sample #3 10/12/2004 2

YES Coal 27

TNNissanSmyrna Boiler 2 Mercury (Hg) Sample #1 3/2/2007 8

YES Coal 27

TNNissanSmyrna Boiler 2 Mercury (Hg) Sample #2 3/2/2007 5

YES Coal 27

TNNissanSmyrna Boiler 2 Mercury (Hg) Sample #3 3/2/2007 3

YES Coal 28

PANorfolkSouthern 031 Mercury (Hg) Sample #1 3/22/2006 8

YES Coal 28

PANorfolkSouthern 031 Mercury (Hg) Sample #2 3/22/2006 6

YES Coal 28

PANorfolkSouthern 031 Mercury (Hg) Sample #3 3/22/2006 5

YES Coal 29

PANorfolkSouthern 032 Mercury (Hg) Sample #1 3/22/2006 8

YES Coal 29

PANorfolkSouthern 032 Mercury (Hg) Sample #2 3/22/2006 6

YES Coal 29

PANorfolkSouthern 032 Mercury (Hg) Sample #3 3/22/2006 5

YES Coal 30

PANorfolkSouthern 033 Mercury (Hg) Sample #1 3/22/2006 8

YES Coal 30

PANorfolkSouthern 033 Mercury (Hg) Sample #2 3/22/2006 6

YES Coal 30

PANorfolkSouthern 033 Mercury (Hg) Sample #3 3/22/2006 5

YES Coal 31

MNRochesterUtilities EU003 Mercury (Hg) Sample #1 5/25/2005 5

YES Coal 31

MNRochesterUtilities EU003 Mercury (Hg) Sample #2 5/25/2005 9
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 31

MNRochesterUtilities EU003 Mercury (Hg) Sample #3 5/25/2005 5

YES Coal 32

VADukeEnergyNarrows Boiler #7 Mercury (Hg) Sample #1 10/14/2004 9

YES Coal 32

VADukeEnergyNarrows Boiler #7 Mercury (Hg) Sample #1 4/16/2004 7

YES Coal 32

VADukeEnergyNarrows Boiler #7 Mercury (Hg) Sample #2 10/14/2004 1

YES Coal 32

VADukeEnergyNarrows Boiler #7 Mercury (Hg) Sample #2 4/16/2004 5

YES Coal 32

VADukeEnergyNarrows Boiler #7 Mercury (Hg) Sample #3 4/16/2004 6

YES Coal 32

VADukeEnergyNarrows Boiler #7 Mercury (Hg) Sample #3 10/14/2004 9

YES Gas 1 1

NCCampLejeuneMCB

C-AS-4151-16 Mercury (Hg) Sample #1 9/30/2009 9

YES Gas 1 1

NCCampLejeuneMCB

C-AS-4151-16 Mercury (Hg) Sample #2 10/1/2009 9

YES Gas 1 1

NCCampLejeuneMCB

C-AS-4151-16 Mercury (Hg) Sample #3 10/1/2009 8

YES Gas 1 2

CAConocoPhilipsLosAng

D146 B-202 U90 Mercury (Hg) Sample #1 4/23/1995 1

YES Gas 1 2

CAConocoPhilipsLosAng

D146 B-202 U90 Mercury (Hg) Sample #2 4/24/1995 1

YES Gas 1 2

CAConocoPhilipsLosAng

D146 B-202 U90 Mercury (Hg) Sample #3 4/25/1995 6

YES Gas 1 yes 1

ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Mercury (Hg) Sample #1 8/26/2009 6
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Gas 1 yes 1

ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Mercury (Hg) Sample #2 8/27/2009 2

YES Gas 1 yes 1

ILUSSGraniteCity

No. 8 Galvanizing Line Furnace Mercury (Hg) Sample #3 8/28/2009 1

YES Gas 2 1

SCBMWManufacturingCo HB03 Mercury (Hg) 1 8/25/2009 DLL 1

YES Gas 2 1

SCBMWManufacturingCo HB03 Mercury (Hg) 2 8/25/2009 DLL 6

YES Gas 2 1

SCBMWManufacturingCo HB03 Mercury (Hg) 3 8/26/2009 DLL 7

YES Liquid 1 MNGPDuluth

EU33 Boiler #3 Mercury (Hg) 1 9/10/2009 DLL 9

YES Liquid 1 MNGPDuluth

EU33 Boiler #3 Mercury (Hg) 2 9/10/2009 DLL 4

YES Liquid 1 MNGPDuluth

EU33 Boiler #3 Mercury (Hg) 3 9/10/2009 DLL 3

YES Liquid 2

MEFPLEnergyWyman Unit #5 Mercury (Hg) PM/TM-R1 10/5/2009 8

YES Liquid 2

MEFPLEnergyWyman Unit #5 Mercury (Hg) PM/TM-R2 10/5/2009 1

YES Liquid 2

MEFPLEnergyWyman Unit #5 Mercury (Hg) PM/TM-R3 10/6/2009 6

YES Liquid 3

PABoeingRidleyPark 033 Mercury (Hg) M29-1 9/22/2009 DLL 1

YES Liquid 3

PABoeingRidleyPark 033 Mercury (Hg) M29-2 9/23/2009 DLL 1

YES Liquid 3

PABoeingRidleyPark 033 Mercury (Hg) M29-3 9/24/2009 DLL 1

YES Liquid 4

NYConEd59thStStationNewYork Boiler 118 Mercury (Hg) 29-1 9/19/2009 1
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid 4

NYConEd59thStStationNewYork Boiler 118 Mercury (Hg) 29-2 9/19/2009 1

YES Liquid 4

NYConEd59thStStationNewYork Boiler 118 Mercury (Hg) 29-3 9/19/2009 1

YES Liquid 5

NJVinelandMuniElectricHowardDown Unit 9 Mercury (Hg) 1 7/20/2009 DLL 3

YES Liquid 5

NJVinelandMuniElectricHowardDown Unit 9 Mercury (Hg) 2 7/20/2009 DLL 4

YES Liquid 5

NJVinelandMuniElectricHowardDown Unit 9 Mercury (Hg) 3 7/21/2009 DLL 3

YES Liquid 8

CTElectric Boat EMU 17 Mercury (Hg) 1 8/18/2009 DLL 7

YES Liquid 8

CTElectric Boat EMU 17 Mercury (Hg) 3 8/19/2009 BDL 7

YES Liquid 8

CTElectric Boat EMU 17 Mercury (Hg) 4 8/19/2009 DLL 7

YES Liquid 9

INUSSteelGaryWorks O4B10459 Mercury (Hg) M29-1 9/9/2009 7

YES Liquid 9

INUSSteelGaryWorks O4B10459 Mercury (Hg) M29-2 9/10/2009 1

YES Liquid 9

INUSSteelGaryWorks O4B10459 Mercury (Hg) M29-3 9/11/2009 1

YES Liquid 16

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) 1 11/17/2009 DLL 7

YES Liquid 16

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) 2 11/17/2009 DLL 6

YES Liquid 16

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) 3 11/18/2009 DLL 6
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

CTElectric Boat EMU 17 Mercury (Hg) Sample #1 4

YES Liquid

CTElectric Boat EMU 18 Mercury (Hg) Sample #1 4

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #1 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #1 3

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #1 6

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #10 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #11 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #12 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #2 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #2 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #2 1

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #3 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #3 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #3 1
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #4 4

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #5 4

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #6 3

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #7 ND 2

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #8 3

YES Liquid

MESDWarrenSomerset

Package Boiler Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #4 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-1, Source #27-0010-05 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #5 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

A15L-2, Source #27-0010-05 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #6 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

B21L-1, Source #27-0010-28 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #7 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D2A-1, Source #27-0010-09 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #8 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-1, Source #27-0010-86 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

D88L-2, Source #27-0010-86 Mercury (Hg) Sample #9 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-1, Source #27-0010-30 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #1 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

F52L-2, Source #27-0010-30 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #10 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I3A-1, Source #27-0010-12 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #11 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I4A-1, Source #27-0010-13 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #12 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #2 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

I5A-1, Source #27-0010-14 Mercury (Hg) Sample #9 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #1 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #10 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #11 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #12 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #2 ND 2
Appendix G-9: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon Non-Detect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #3 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #4 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #5 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #6 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #7 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #8 ND 2

YES Liquid

TNMilanArmyAmmunitionPlant

K313A-1, Source #27-0010-83 Mercury (Hg) Sample #9 ND 2
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Biomass 1

ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) 1 9/8/2009 < 3.61E-

YES Biomass 1

ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) 2 9/8/2009 < 3.69E-

YES Biomass 1

ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) 3 9/8/2009 < 3.78E-

YES Biomass 1

ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) Sample #1 8/8/2006 8.00E-

YES Biomass 1

ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) Sample #2 8/8/2006 2.10E-

YES Biomass 1

ARPotlatchForestWarren

Wellons Boiler

Hydrogen Chloride (HCl) Sample #3 9/8/2006 1.80E-

YES Biomass 2

WABoisePaperWallula

Hog Fuel Boiler

Hydrogen Chloride (HCl) Sample #1 5/6/2008 8.67E-

YES Biomass 2

WABoisePaperWallula

Hog Fuel Boiler

Hydrogen Chloride (HCl) Sample #2 5/6/2008 1.62E-

YES Biomass 2

WABoisePaperWallula

Hog Fuel Boiler

Hydrogen Chloride (HCl) Sample #3 5/6/2008 ND 1.93E-

YES Biomass 3

FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #1 12/16/2002 2.32E-

YES Biomass 3

FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #1 1/19/2005 1.55E-

YES Biomass 3

FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #2 12/16/2002 2.15E-

YES Biomass 3

FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride 

(HCl) Sample #2 1/19/2005 1.69E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Biomass 3

FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #3 1/19/2005 1.22E-

YES Biomass 3

FLSugarCaneGrowersCoop Boiler No. 8

Hydrogen Chloride (HCl) Sample #3 12/16/2002 1.51E-

YES Biomass 4

ARAnthonyForestProducts SN-12

Hydrogen Chloride (HCl) Sample #1 9/1/2009 2.10E-

YES Biomass 4

ARAnthonyForestProducts SN-12

Hydrogen Chloride (HCl) Sample #2 9/1/2009 2.30E-

YES Biomass 4

ARAnthonyForestProducts SN-12

Hydrogen Chloride (HCl) Sample #3 9/2/2009 1.60E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #1 8/14/2009 3.20E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #1 6/22/2006 6.43E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #1 8/14/2009 2.00E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #2 6/22/2006 4.84E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #2 8/14/2009 2.60E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #2 8/14/2009 2.00E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #3 8/14/2009 2.00E-

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #3 6/22/2006 2.22E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Biomass 5

WAGraysHarborPaper

No. 6 Boiler (EU2)

Hydrogen Chloride (HCl) Sample #3 8/14/2009 1.80E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #1 12/1/2006 2.70E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #1 12/1/2006 2.70E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #1 12/10/2002 2.30E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #2 12/10/2002 1.50E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #2 12/1/2006 2.40E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #2 12/1/2006 2.40E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #3 12/1/2006 1.90E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #3 12/10/2002 2.27E-

YES Biomass 6

FLUSSugarCorp Boiler No. 4

Hydrogen Chloride (HCl) Sample #3 12/1/2006 1.90E-

YES Biomass 7

MSHoodWaynesboro

AA-001 (Wood-Fired Boiler)

Hydrogen Chloride (HCl) Sample #1 10/14/2003 2.80E-

YES Biomass 7

MSHoodWaynesboro

AA-001 (Wood-Fired Boiler)

Hydrogen Chloride (HCl) Sample #2 10/14/2003 2.35E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Biomass 7

MSHoodWaynesboro

AA-001 (Wood-Fired Boiler)

Hydrogen Chloride (HCl) Sample #3 10/14/2003 1.18E-

YES Coal 1

INAlcoaWarrick Unit #3

Hydrogen Chloride (HCl) Sample #1 8/7/2008 ND 1.43E-

YES Coal 1

INAlcoaWarrick Unit #3

Hydrogen Chloride (HCl) Sample #2 8/7/2008 ND 1.57E-

YES Coal 2

IDTASCOPaul

Erie City Boiler

Hydrogen Chloride (HCl) Sample #1 6/20/2006 ND 3.96E-

YES Coal 2

IDTASCOPaul

Erie City Boiler

Hydrogen Chloride (HCl) Sample #2 6/20/2006 ND 4.02E-

YES Coal 2

IDTASCOPaul

Erie City Boiler

Hydrogen Chloride (HCl) Sample #3 6/21/2006 ND 3.58E-

YES Coal 3

INAlcoaWarrick Unit #2

Hydrogen Chloride (HCl) Sample #1 8/6/2008 ND 1.51E-

YES Coal 3

INAlcoaWarrick Unit #2

Hydrogen Chloride (HCl) Sample #2 8/6/2008 1.03E-

YES Coal 4

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

Hydrogen Chloride (HCl) 1 6/2/2009 8.56E-

YES Coal 4

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

Hydrogen Chloride (HCl) 2 6/2/2009 6.85E-

YES Coal 4

IARoquetteAmerica

Circulating Fluidized Bed Boiler (121)

Hydrogen Chloride (HCl) 3 6/3/2009 3.13E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 5

TNEastman_NO_CBIDATA Boiler 30

Hydrogen Chloride (HCl) Sample #1 8/26/2009 ND 7.30E-

YES Coal 5

TNEastman_NO_CBIDATA Boiler 30

Hydrogen Chloride (HCl) Sample #2 8/27/2009 ND 7.30E-

YES Coal 5

TNEastman_NO_CBIDATA Boiler 30

Hydrogen Chloride (HCl) Sample #3 8/27/2009 ND 7.10E-

YES Coal 6

AZCatalystPaperSnowflake

Power Boiler #2 Coal

Hydrogen Chloride (HCl) Sample #1 3/24/2006 1.83E-

YES Coal 6

AZCatalystPaperSnowflake

Power Boiler #2 Coal

Hydrogen Chloride (HCl) Sample #2 3/24/2006 7.69E-

YES Coal 6

AZCatalystPaperSnowflake

Power Boiler #2 Coal

Hydrogen Chloride (HCl) Sample #3 3/24/2006 8.86E-

YES Coal 7

MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #1 12/6/2005 8.48E-

YES Coal 7

MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #1 10/4/2006 1.79E-

YES Coal 7

MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #2 12/6/2005 3.81E-

YES Coal 7

MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #2 10/4/2006 2.27E-

YES Coal 7

MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #3 12/6/2005 3.38E-

YES Coal 7

MOJamesRiverPowerStation Unit 1

Hydrogen Chloride (HCl) Sample #3 10/4/2006 2.30E-

YES Coal 8

MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #1 10/4/2006 1.79E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 8

MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #1 12/6/2005 8.48E-

YES Coal 8

MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #2 10/4/2006 2.27E-

YES Coal 8

MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #2 12/6/2005 3.81E-

YES Coal 8

MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #3 12/6/2005 3.38E-

YES Coal 8

MOJamesRiverPowerStation Unit 2

Hydrogen Chloride (HCl) Sample #3 10/4/2006 2.30E-

YES Coal 9

ALIPCourtland

No.2 Combination Boiler / 11CU201

Hydrogen Chloride (HCl) Sample #1 9/10/1996 3.86E-

YES Coal 9

ALIPCourtland

No.2 Combination Boiler / 11CU201

Hydrogen Chloride (HCl) Sample #2 9/10/1996 ND 2.55E-

YES Coal 9

ALIPCourtland

No.2 Combination Boiler / 11CU201

Hydrogen Chloride (HCl) Sample #3 9/10/1996 ND 2.06E-

YES Coal 10

IDTASCOPaul

Babcock and Wilcox (B&W) Boiler

Hydrogen Chloride (HCl) Sample #1 6/1/2006 ND 3.00E-

YES Coal 11

NDMinnDakFarmers

Babcock and Wilcox Boiler #5

Hydrogen Chloride (HCl) Sample #1 10/26/2006 5.14E-

YES Coal 11

NDMinnDakFarmers

Babcock and Wilcox Boiler #5

Hydrogen Chloride (HCl) Sample #2 10/26/2006 2.77E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 11

NDMinnDakFarmers

Babcock and Wilcox Boiler #5

Hydrogen Chloride (HCl) Sample #3 10/26/2006 3.03E-

YES Coal 12

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Hydrogen Chloride (HCl) Sample #1 8/24/2009 ND 3.81E-

YES Coal 12

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Hydrogen Chloride (HCl) Sample #2 8/24/2009 ND 3.77E-

YES Coal 12

IAArchersDanielsMidlandDesMoines

Asea Boiler #1

Hydrogen Chloride (HCl) Sample #3 8/25/2009 ND 4.07E-

YES Coal 13

VAUniversityofVirginia 7103-1-01R

Hydrogen Chloride (HCl) M26A-1 9/15/2009 < 5.80E-

YES Coal 13

VAUniversityofVirginia 7103-1-01R

Hydrogen Chloride (HCl) M26A-2 9/16/2009 5.91E-

YES Coal 13

VAUniversityofVirginia 7103-1-01R

Hydrogen Chloride (HCl) M26A-3 9/17/2009 < 5.37E-

YES Coal 14

WINewPageBiron B24

Hydrogen Chloride (HCl) 1 8/25/2009 2.00E-

YES Coal 14

WINewPageBiron B24

Hydrogen Chloride (HCl) 2 9/22/2009 1.95E-

YES Coal 14

WINewPageBiron B24

Hydrogen Chloride (HCl) 3 9/22/2009 2.18E-

YES Coal 14

WINewPageBiron B24

Hydrogen Chloride (HCl) Sample #1 9/12/2007 5.40E-

YES Coal 14

WINewPageBiron B24

Hydrogen Chloride (HCl) Sample #2 9/12/2007 5.20E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 14

WINewPageBiron B24

Hydrogen Chloride (HCl) Sample #3 9/12/2007 7.00E-

YES Coal 15

MICityofEscanaba

EUBOILER#1

Hydrogen Chloride (HCl) Sample #1 10/27/2004 6.00E-

YES Coal 15

MICityofEscanaba

EUBOILER#1

Hydrogen Chloride (HCl) Sample #2 10/27/2004 6.00E-

YES Coal 15

MICityofEscanaba

EUBOILER#1

Hydrogen Chloride (HCl) Sample #3 10/27/2004 6.00E-

YES Coal 16

VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #1 9/26/2009 7.40E-

YES Coal 16

VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #2 9/26/2009 5.04E-

YES Coal 16

VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #3 9/26/2009 7.62E-

YES Coal 16

VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #1 11/8/2004 8.68E-

YES Coal 16

VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #2 11/8/2004 6.24E-

YES Coal 16

VASmurfitStoneWestpt PB08

Hydrogen Chloride (HCl) Sample #3 11/8/2004 7.22E-

YES Coal 17

TNEastman_NO_CBIDATA Boiler 31

Hydrogen Chloride (HCl) Sample #1 3/15/2005 ND 7.00E-

YES Coal 17

TNEastman_NO_CBIDATA Boiler 31

Hydrogen Chloride (HCl) Sample #2 3/15/2005 ND 7.00E-

YES Coal 17

TNEastman_NO_CBIDATA Boiler 31

Hydrogen Chloride (HCl) Sample #3 3/15/2005 ND 7.00E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 18

WINewPageWisconsinRapids

Power Boiler 1 - B21

Hydrogen Chloride (HCl) Sample #1 12/14/2005 3.00E-

YES Coal 18

WINewPageWisconsinRapids

Power Boiler 1 - B21

Hydrogen Chloride (HCl) Sample #2 12/15/2005 1.40E-

YES Coal 18

WINewPageWisconsinRapids

Power Boiler 1 - B21

Hydrogen Chloride (HCl) Sample #3 12/15/2005 7.00E-

YES Coal 19

PADomtarJohnsonburg

#81 Coal Boiler

Hydrogen Chloride (HCl) Sample #1 7/18/2007 8.00E-

YES Coal 19

PADomtarJohnsonburg

#81 Coal Boiler

Hydrogen Chloride (HCl) Sample #2 7/18/2007 1.00E-

YES Coal 19

PADomtarJohnsonburg

#81 Coal Boiler

Hydrogen Chloride (HCl) Sample #3 7/17/2007 7.00E-

YES Coal 20

PADomtarJohnsonburg

#82 Coal Boiler

Hydrogen Chloride (HCl) Sample #1 7/18/2007 8.00E-

YES Coal 20

PADomtarJohnsonburg

#82 Coal Boiler

Hydrogen Chloride (HCl) Sample #2 7/18/2007 1.00E-

YES Coal 20

PADomtarJohnsonburg

#82 Coal Boiler

Hydrogen Chloride (HCl) Sample #3 7/17/2007 7.00E-

YES Coal 21

IDTASCONampa

Babcock and Wilcox (B&W) #1

Hydrogen Chloride (HCl) Sample #1 12/5/2006 9.00E-

YES Coal 21

IDTASCONampa

Babcock and Wilcox (B&W) #1

Hydrogen Chloride (HCl) Sample #2 12/5/2006 9.00E-

YES Coal 21

IDTASCONampa

Babcock and Wilcox (B&W) #1

Hydrogen Chloride (HCl) Sample #3 12/5/2006 9.00E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 22

IDTASCONampa

Babcock and Wilcox (B&W) #2

Hydrogen Chloride (HCl) Sample #1 12/5/2006 9.00E-

YES Coal 22

IDTASCONampa

Babcock and Wilcox (B&W) #2

Hydrogen Chloride (HCl) Sample #2 12/5/2006 9.00E-

YES Coal 22

IDTASCONampa

Babcock and Wilcox (B&W) #2

Hydrogen Chloride (HCl) Sample #3 12/5/2006 9.00E-

YES Coal 23

WINewPageWisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #1 5/22/2003 9.90E-

YES Coal 23

WINewPageWisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #1 5/21/2003 8.00E-

YES Coal 23

WINewPageWisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #2 5/21/2003 1.10E-

YES Coal 23

WINewPageWisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #2 5/22/2003 ND 1.00E-

YES Coal 23

WINewPageWisconsinRapids

Power Boiler 2 - B20

Hydrogen Chloride (HCl) Sample #3 5/21/2003 8.00E-

YES Coal 24

IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #1 4/22/2004 9.67E-

YES Coal 24

IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #1 4/22/2004 5.50E-

YES Coal 24

IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #2 4/22/2004 1.16E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 24

IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #2 4/22/2004 4.20E-

YES Coal 24

IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #3 4/22/2004 3.70E-

YES Coal 24

IAMuscatinePowerandWater Unit 7

Hydrogen Chloride (HCl) Sample #3 4/22/2004 1.30E-

YES Coal 25

IDAmalgamatedSugarCoTwinFalls S-B2

Hydrogen Chloride (HCl) Sample #1 9/28/2006 2.00E-

YES Coal 25

IDAmalgamatedSugarCoTwinFalls S-B2

Hydrogen Chloride (HCl) Sample #2 9/28/2006 1.00E-

YES Coal 25

IDAmalgamatedSugarCoTwinFalls S-B2

Hydrogen Chloride (HCl) Sample #3 9/28/2006 1.00E-

YES Coal 26

OHPainesvilleMunicipalElectric B004

Hydrogen Chloride (HCl) Sample #1 8/23/2006 1.00E-

YES Coal 26

OHPainesvilleMunicipalElectric B004

Hydrogen Chloride (HCl) Sample #2 8/23/2006 1.00E-

YES Coal 26

OHPainesvilleMunicipalElectric B004

Hydrogen Chloride (HCl) Sample #3 8/23/2006 2.00E-

YES Coal 27

MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #1 2/9/2005 1.46E-

YES Coal 27

MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #1 7/13/2006 1.39E-

YES Coal 27

MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #2 2/9/2005 1.41E-

YES Coal 27

MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #2 7/13/2006 1.37E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 27

MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #3 2/9/2005 1.47E-

YES Coal 27

MIPharma&Upjohn1180 Boiler 3

Hydrogen Chloride (HCl) Sample #3 7/13/2006 1.40E-

YES Coal 28

WYGeneralChemical

GR-2-L (C BOILER)

Hydrogen Chloride (HCl) Sample #1 10/27/2004 1.70E-

YES Coal 28

WYGeneralChemical

GR-2-L (C BOILER)

Hydrogen Chloride (HCl) Sample #2 10/27/2004 1.70E-

YES Coal 28

WYGeneralChemical

GR-2-L (C BOILER)

Hydrogen Chloride (HCl) Sample #3 10/27/2004 2.00E-

YES Coal 29

TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #1 3/10/2005 2.00E-

YES Coal 29

TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #1 3/9/2005 1.60E-

YES Coal 29

TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #2 3/9/2005 2.00E-

YES Coal 29

TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #2 3/10/2005 3.20E-

YES Coal 29

TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #3 3/10/2005 8.30E-

YES Coal 29

TNEastman_NO_CBIDATA Boiler 27

Hydrogen Chloride (HCl) Sample #3 3/9/2005 2.00E-

YES Coal 30

ILPrairiePowerPearl B1

Hydrogen Chloride (HCl) Sample #1 5/4/2005 2.00E-

YES Coal 30

ILPrairiePowerPearl B1

Hydrogen Chloride (HCl) Sample #2 5/4/2005 1.90E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 30

ILPrairiePowerPearl B1

Hydrogen Chloride (HCl) Sample #3 5/4/2005 1.90E-

YES Coal 31

WYGeneralChemical

GR-3-W (D BOILER)

Hydrogen Chloride (HCl) Sample #1 10/21/2004 2.00E-

YES Coal 31

WYGeneralChemical

GR-3-W (D BOILER)

Hydrogen Chloride (HCl) Sample #2 10/21/2004 2.00E-

YES Coal 31

WYGeneralChemical

GR-3-W (D BOILER)

Hydrogen Chloride (HCl) Sample #3 10/21/2004 1.90E-

YES Coal 32

MNAmericanCrystalMoorhead Boiler 3

Hydrogen Chloride (HCl) Sample #1 11/16/2004 8.93E-

YES Coal 32

MNAmericanCrystalMoorhead Boiler 3

Hydrogen Chloride (HCl) Sample #2 11/16/2004 2.89E-

YES Coal 32

MNAmericanCrystalMoorhead Boiler 3

Hydrogen Chloride (HCl) Sample #3 11/16/2004 2.20E-

YES Coal 33

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #1 5/28/2004 4.00E-

YES Coal 33

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #1 8/4/2006 2.00E-

YES Coal 33

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #2 8/4/2006 2.00E-

YES Coal 33

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #2 5/28/2004 1.20E-

YES Coal 33

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #3 5/28/2004 6.00E-

YES Coal 33

OHPainesvilleMunicipalElectric B003

Hydrogen Chloride (HCl) Sample #3 8/4/2006 2.00E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 34

INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #1 4/6/2005 3.17E-

YES Coal 34

INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #1 6/27/2006 3.30E-

YES Coal 34

INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #2 6/27/2006 5.50E-

YES Coal 34

INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #2 4/6/2005 1.75E-

YES Coal 34

INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #3 4/6/2005 3.05E-

YES Coal 34

INSABICInnovativePlastics

09-002 Erie Boiler

Hydrogen Chloride (HCl) Sample #3 6/27/2006 5.90E-

YES Coal 35

INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #1 4/7/2005 3.17E-

YES Coal 35

INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #1 6/27/2006 3.30E-

YES Coal 35

INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #2 4/7/2005 1.75E-

YES Coal 35

INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #2 6/27/2006 5.50E-

YES Coal 35

INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #3 6/27/2006 5.90E-

YES Coal 35

INSABICInnovativePlastics

09-002 Lasker Boiler

Hydrogen Chloride (HCl) Sample #3 4/7/2005 3.05E-

YES Coal 36

WINewPageWhiting B24

Hydrogen Chloride (HCl) Sample #1 8/24/2006 2.00E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Coal 36

WINewPageWhiting B24

Hydrogen Chloride (HCl) Sample #2 8/24/2006 3.30E-

YES Coal 36

WINewPageWhiting B24

Hydrogen Chloride (HCl) Sample #3 8/24/2006 2.90E-

YES Gas 1 1

SCMichelinSandySprings B:02:01

Hydrogen Chloride (HCl) Sample #1 9/10/2009 1.14E-

YES Gas 1 1

SCMichelinSandySprings B:02:01

Hydrogen Chloride (HCl) Sample #2 9/10/2009 ND 3.84E-

YES Gas 1 1

SCMichelinSandySprings B:02:01

Hydrogen Chloride (HCl) Sample #3 9/10/2009 ND 6.56E-

YES Gas 1 2

WYSinclairWyoming

Pt 74 #2 H2 Plant Heater

Hydrogen Chloride (HCl) 1 11/18/2009 DL 1.26E-

YES Gas 1 2

WYSinclairWyoming

Pt 74 #2 H2 Plant Heater

Hydrogen Chloride (HCl) 2 11/18/2009 DL 1.30E-

YES Gas 1 2

WYSinclairWyoming

Pt 74 #2 H2 Plant Heater

Hydrogen Chloride (HCl) 3 11/18/2009 DL 1.30E-

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088

Hydrogen Chloride (HCl) M26-1 8/13/2009 9.81E-

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088

Hydrogen Chloride (HCl) M26-2 8/14/2009 8.39E-

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088

Hydrogen Chloride (HCl) M26-3 8/14/2009 7.58E-

YES Gas 1 yes 2

INAlcoaWarrick

Annealing Furnace #15

Hydrogen Chloride (HCl) M26A-1 8/17/2009 BDL 2.54E-

YES Gas 1 yes 2

INAlcoaWarrick

Annealing Furnace #15

Hydrogen Chloride (HCl) M26A-2 8/17/2009 BDL 2.34E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Gas 1 yes 2

INAlcoaWarrick

Annealing Furnace #15

Hydrogen Chloride (HCl) M26A-3 8/17/2009 BDL 2.48E-

YES Gas 2 1

LAShellChemicaGeismar

Furnace FS801

Hydrogen Chloride (HCl) Sample #1 8/25/2009 ND 1.57E-

YES Gas 2 1

LAShellChemicaGeismar

Furnace FS801

Hydrogen Chloride (HCl) Sample #2 8/26/2009 ND 1.85E-

YES Gas 2 1

LAShellChemicaGeismar

Furnace FS801

Hydrogen Chloride (HCl) Sample #3 8/27/2009 ND 1.68E-

YES Liquid 2

TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #1 7/29/2009 ND 6.18E-

YES Liquid 2

TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #1 8/31/2006 1.95E-

YES Liquid 2

TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #2 7/30/2009 ND 6.19E-

YES Liquid 2

TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #2 8/31/2006 2.09E-

YES Liquid 2

TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #3 7/30/2009 ND 6.24E-

YES Liquid 2

TNInvistaChattanooga

EU003 - Vaporizer #2

Hydrogen Chloride (HCl) Sample #3 8/31/2006 1.28E-

YES Liquid 3

INUSSteelGaryWorks O4B10459

Hydrogen Chloride (HCl) M26A-1 9/8/2009 2.33E-

YES Liquid 3

INUSSteelGaryWorks O4B10459

Hydrogen Chloride (HCl) M26A-2 9/8/2009 1.88E-

YES Liquid 3

INUSSteelGaryWorks O4B10459

Hydrogen Chloride (HCl) M26A-3 9/8/2009 1.99E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid 4

VAINVISTAWaynesboro

2-205 (V#1) Vaporizer #1

Hydrogen Chloride (HCl) Sample #1 4/18/2008 3.15E-

YES Liquid 4

VAINVISTAWaynesboro

2-205 (V#1) Vaporizer #1

Hydrogen Chloride (HCl) Sample #2 4/18/2008 2.07E-

YES Liquid 4

VAINVISTAWaynesboro

2-205 (V#1) Vaporizer #1

Hydrogen Chloride (HCl) Sample #3 4/18/2008 2.08E-

YES Liquid

CTElectric Boat EMU 18 Chlorine (Cl) Sample #1 ND 5.60E-

YES Liquid

NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-HP-738-59 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-LCH-4022-19 Chlorine (Cl) Sample #3 ND 2.65E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-MG-SH8-58 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-38 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-39 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #1 ND 2.65E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-230-40 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-72 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-73 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #1 ND 2.65E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-MP-625-74 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-01 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-02 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #2 ND 2.65E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-100-05 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-118-03 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB A-NH-120-04 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #2 ND 2.65E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-120-H4 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-NH-121-H1 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-08 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #3 ND 2.65E-
Appendix G-10: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Metals 

Process 

Heater? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn? lb/mmB

YES Liquid

NCCampLejeuneMCB

A-PP-1943-H7 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #1 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #2 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #3 ND 2.65E-

YES Liquid

NCCampLejeuneMCB

A-PP-2615-09 Chlorine (Cl) Sample #3 ND 2.65E-
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 1

OKVRCOklahoma H-101 CO Sample #3 10/22/1998 9.36E-03 -4.

YES Gas 1 2

OKVRCOklahoma H-102A CO Sample #1 10/20/1998 3.46E-01 -1.

YES Gas 1 2

OKVRCOklahoma H-102A CO Sample #1 10/21/1998 1.01E-02 -4.

YES Gas 1 2

OKVRCOklahoma H-102A CO Sample #2 12/3/1997 1.74E-01 -1.

YES Gas 1 2

OKVRCOklahoma H-102A CO Sample #2 12/3/1997 1.04E-01 -2.

YES Gas 1 2

OKVRCOklahoma H-102A CO Sample #2 10/20/1998 9.43E+00 2.

YES Gas 1 2

OKVRCOklahoma H-102A CO Sample #3 10/20/1998 2.04E+01 3.

YES Gas 1 3

TXRohmHaasDeerPark ACET-2B-4 CO Sample #1 11/29/2006 ND 1.00E-02 -4.

YES Gas 1 3

TXRohmHaasDeerPark ACET-2B-4 CO Sample #1 11/30/2006 1.96E+00 6

YES Gas 1 3

TXRohmHaasDeerPark ACET-2B-4 CO Sample #2 11/29/2006 ND 2.00E-02 -3.

YES Gas 1 3

TXRohmHaasDeerPark ACET-2B-4 CO Sample #2 11/30/2006 4.16E+00 1.

YES Gas 1 3

TXRohmHaasDeerPark ACET-2B-4 CO Sample #3 11/30/2006 4.91E+00 1.

YES Gas 1 3

TXRohmHaasDeerPark ACET-2B-4 CO Sample #3 11/29/2006 ND 1.00E-02 -4.

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #1 6/4/2008 1.19E+01 2.

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #1 7/7/2006 6.40E-01 -4

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #1 10/5/2006 3.00E-01 -1.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #1 5/9/2007 1.16E+00 1

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #2 5/11/2006 1.00E-02 -4.

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #2 5/24/2006 4.00E-02 -3.

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #2 10/5/2006 1.56E+00 4

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #2 5/9/2007 9.60E-01 -4

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #3 5/9/2007 1.23E+00 2

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #3 5/11/2006 3.00E-02 -3.

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #3 5/24/2006 2.24E+00 8

YES Gas 1 4

OKConocoPhillipsPoncaCity H-9902 CO Sample #3 10/5/2006 2.57E+00 9

YES Gas 1 5

TXDiamondShamrockThreeRivers H-201 CO Sample #1 7/3/1997 2.71E-02 -3.

YES Gas 1 5

TXDiamondShamrockThreeRivers H-201 CO Sample #2 7/3/1997 2.71E-02 -3.

YES Gas 1 5

TXDiamondShamrockThreeRivers H-201 CO Sample #3 7/3/1997 2.71E-02 -3.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 6

TXDiamondShamrockThreeRivers H-203 CO Sample #1 7/3/1997 2.71E-02 -3.

YES Gas 1 6

TXDiamondShamrockThreeRivers H-203 CO Sample #2 7/3/1997 2.71E-02 -3.

YES Gas 1 6

TXDiamondShamrockThreeRivers H-203 CO Sample #3 7/3/1997 2.71E-02 -3.

YES Gas 1 7

TXDiamondShamrockThreeRivers H-204 CO Sample #1 7/3/1997 2.71E-02 -3.

YES Gas 1 7

TXDiamondShamrockThreeRivers H-204 CO Sample #2 7/3/1997 2.71E-02 -3.

YES Gas 1 7

TXDiamondShamrockThreeRivers H-204 CO Sample #3 7/3/1997 2.71E-02 -3.

YES Gas 1 8

VAWesternRefiningYorktown F-562 CO Sample #1 3/7/2007 3.94E-02 -3.

YES Gas 1 9

OKConocoPhillipsPoncaCity H-9851 CO Sample #1 6/5/2008 4.00E-02 -3.

YES Gas 1 9

OKConocoPhillipsPoncaCity H-9851 CO Sample #1 5/4/2006 5.00E-02 -3.

YES Gas 1 9

OKConocoPhillipsPoncaCity H-9851 CO Sample #2 5/4/2006 1.10E-01 -2.

YES Gas 1 9

OKConocoPhillipsPoncaCity H-9851 CO Sample #3 5/4/2006 1.00E-01 -2.

YES Gas 1 10

INBPWhitingRefinery B-601 CO Sample #1 8/20/2007 1.10E-01 -2.

YES Gas 1 10

INBPWhitingRefinery B-601 CO Sample #2 8/20/2007 ND 1.00E-02 -4.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 10

INBPWhitingRefinery B-601 CO Sample #3 8/20/2007 ND 1.00E-02 -4.

YES Gas 1 11

OKConocoPhillipsPoncaCity H-0016 CO Sample #1 4/6/2005 6.00E-02 -2.

YES Gas 1 11

OKConocoPhillipsPoncaCity H-0016 CO Sample #2 4/6/2005 2.00E-02 -3.

YES Gas 1 11

OKConocoPhillipsPoncaCity H-0016 CO Sample #3 4/6/2005 5.00E-02 -3.

YES Gas 1 12

TXOccidentalChemGregory

VCM Plant 1 Furnace 1 CO Sample #1 3/5/1991 ND 5.06E-02 -2.

YES Gas 1 12

TXOccidentalChemGregory

VCM Plant 1 Furnace 1 CO Sample #2 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 12

TXOccidentalChemGregory

VCM Plant 1 Furnace 1 CO Sample #3 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 13

TXOccidentalChemGregory

VCM Plant 1 Furnace 2 CO Sample #1 3/5/1991 ND 5.06E-02 -2.

YES Gas 1 13

TXOccidentalChemGregory

VCM Plant 1 Furnace 2 CO Sample #2 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 13

TXOccidentalChemGregory

VCM Plant 1 Furnace 2 CO Sample #3 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 14

TXOccidentalChemGregory

VCM Plant 1 Furnace 3 CO Sample #1 3/5/1991 ND 5.06E-02 -2.

YES Gas 1 14

TXOccidentalChemGregory

VCM Plant 1 Furnace 3 CO Sample #2 3/5/1991 ND 5.00E-02 -3.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 14

TXOccidentalChemGregory

VCM Plant 1 Furnace 3 CO Sample #3 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 15

TXOccidentalChemGregory

VCM Plant 1 Furnace 4 CO Sample #1 3/5/1991 ND 5.06E-02 -2.

YES Gas 1 15

TXOccidentalChemGregory

VCM Plant 1 Furnace 4 CO Sample #2 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 15

TXOccidentalChemGregory

VCM Plant 1 Furnace 4 CO Sample #3 3/5/1991 ND 5.00E-02 -3.

YES Gas 1 16

MSChevronPascagoula F-2103 CO Sample #1 3/27/2008 5.41E-02 -2.

YES Gas 1 16

MSChevronPascagoula F-2103 CO Sample #2 3/27/2008 5.41E-02 -2.

YES Gas 1 16

MSChevronPascagoula F-2103 CO Sample #3 3/27/2008 5.41E-02 -2.

YES Gas 1 17

TXDiamondShamrockThreeRivers H-1102 CO Sample #1 7/9/1997 6.77E-02 -2.

YES Gas 1 17

TXDiamondShamrockThreeRivers H-1102 CO Sample #2 7/9/1997 6.77E-02 -2.

YES Gas 1 17

TXDiamondShamrockThreeRivers H-1102 CO Sample #3 7/9/1997 5.41E-02 -2.

YES Gas 1 18

NJSunocoWestville Boiler #8 CO Sample #1 10/15/2007 7.89E-02 -2.

YES Gas 1 18

NJSunocoWestville Boiler #8 CO Sample #2 10/15/2007 7.89E-02 -2.

YES Gas 1 18

NJSunocoWestville Boiler #8 CO Sample #3 10/15/2007 3.95E-02 -3.

YES Gas 1 19

KYCatlettsburgRefining 2-23-B-4 CO Sample #1 4/21/2004 4.12E-01 -8

YES Gas 1 19

KYCatlettsburgRefining 2-23-B-4 CO Sample #1 8/12/2005 ND 7.72E-02 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 19

KYCatlettsburgRefining 2-23-B-4 CO Sample #2 8/12/2005 ND 7.77E-02 -2.

YES Gas 1 19

KYCatlettsburgRefining 2-23-B-4 CO Sample #3 8/12/2005 ND 7.75E-02 -2.

YES Gas 1 20

ILWoodRiverRefinery

HTR-DU1-F302 CO Sample #1 4/11/2006 7.88E-02 -2.

YES Gas 1 21

PASunocoMarcusHook

705 (12-4 LSG Heater, H01) CO Sample #1 2/4/2008 8.00E-02 -2.

YES Gas 1 22

OKVRCOklahoma H-201 CO Sample #1 6/22/2005 7.77E-02 -2.

YES Gas 1 22

OKVRCOklahoma H-201 CO Sample #1 6/22/2005 1.84E+02 5.

YES Gas 1 22

OKVRCOklahoma H-201 CO Sample #2 6/22/2005 9.15E-02 -2.

YES Gas 1 22

OKVRCOklahoma H-201 CO Sample #2 6/22/2005 5.56E+01 4.

YES Gas 1 22

OKVRCOklahoma H-201 CO Sample #3 6/22/2005 9.04E-02 -2.

YES Gas 1 23

LACitgoLakeCharles EQT242 CO Sample #1 6/12/2003 8.95E-02 -2.

YES Gas 1 24 INNucorSteel

Cold Mill Annealing CO Sample #1 6/24/2004 1.75E-01 -1.

YES Gas 1 24 INNucorSteel

Cold Mill Annealing CO Sample #2 8/19/2009 9.01E-02 -2.

YES Gas 1 25

MSChevronPascagoula F-6701 CO Sample #1 2/27/2007 1.21E-01 -2.

YES Gas 1 25

MSChevronPascagoula F-6701 CO Sample #2 2/27/2007 8.06E-02 -2.

YES Gas 1 25

MSChevronPascagoula F-6701 CO Sample #3 2/27/2007 7.95E-02 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #1 6/9/2008 ND 9.83E-02 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #1 6/12/2007 ND 1.06E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #1 6/13/2006 ND 1.12E-01 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #2 6/9/2008 ND 9.92E-02 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #2 6/12/2007 ND 1.07E-01 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #2 6/13/2006 ND 1.13E-01 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #3 6/13/2006 ND 1.12E-01 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #3 6/9/2008 ND 1.00E-01 -2.

YES Gas 1 26

KYCatlettsburgRefining 2-122-B-1 CO Sample #3 6/12/2007 ND 1.08E-01 -2.

YES Gas 1 27

ALHuntRefining HS-2041A CO Sample #1 6/17/2008 1.00E-01 -2.

YES Gas 1 28

ALHuntRefining HS-2041B CO Sample #1 6/17/2008 1.00E-01 -2.

YES Gas 1 29

ALHuntRefining HS-2041C CO Sample #1 6/17/2008 1.00E-01 -2.

YES Gas 1 30

OKConocoPhillipsPoncaCity H-0003 CO Sample #1 4/12/2002 1.60E-01 -1.

YES Gas 1 30

OKConocoPhillipsPoncaCity H-0003 CO Sample #2 4/12/2002 4.00E-02 -3.

YES Gas 1 31

TXAirProductsBaytown

BOILER (EPN 7) CO Sample #1 1/19/2006 1.00E-01 -2.

YES Gas 1 31

TXAirProductsBaytown

BOILER (EPN 7) CO Sample #2 1/19/2006 1.00E-01 -2.

YES Gas 1 31

TXAirProductsBaytown

BOILER (EPN 7) CO Sample #3 1/19/2006 ND 1.00E-01 -2.

YES Gas 1 32

TXChevronBaytown H-1001 CO Sample #1 6/4/2004 ND 1.00E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 32

TXChevronBaytown H-1001 CO Sample #2 6/4/2004 ND 1.00E-01 -2.

YES Gas 1 32

TXChevronBaytown H-1001 CO Sample #3 6/4/2004 ND 1.00E-01 -2.

YES Gas 1 33

TXEquistarPasadena Boiler (P-25) CO Sample #1 12/6/2007 ND 1.00E-01 -2.

YES Gas 1 33

TXEquistarPasadena Boiler (P-25) CO Sample #2 12/6/2007 ND 1.00E-01 -2.

YES Gas 1 33

TXEquistarPasadena Boiler (P-25) CO Sample #3 12/6/2007 ND 1.00E-01 -2.

YES Gas 1 34

TXValeroTexasCity

Heater 13-1451 CO Sample #1 8/15/2000 ND 1.00E-01 -2.

YES Gas 1 34

TXValeroTexasCity

Heater 13-1451 CO Sample #2 8/15/2000 ND 1.00E-01 -2.

YES Gas 1 34

TXValeroTexasCity

Heater 13-1451 CO Sample #3 8/15/2000 ND 1.00E-01 -2.

YES Gas 1 35

TXValeroTexasCity Heater 16 CO Sample #1 11/1/1999 ND 1.00E-01 -2.

YES Gas 1 35

TXValeroTexasCity Heater 16 CO Sample #2 11/1/1999 ND 1.00E-01 -2.

YES Gas 1 35

TXValeroTexasCity Heater 16 CO Sample #3 11/1/1999 ND 1.00E-01 -2.

YES Gas 1 36

TXValeroTexasCity Heater 17 CO Sample #1 11/1/1999 ND 1.00E-01 -2.

YES Gas 1 36

TXValeroTexasCity Heater 17 CO Sample #2 11/1/1999 ND 1.00E-01 -2.

YES Gas 1 36

TXValeroTexasCity Heater 17 CO Sample #3 11/1/1999 ND 1.00E-01 -2.

YES Gas 1 37

TXValeroTexasCity Heater 28 CO Sample #1 10/31/2002 ND 1.00E-01 -2.

YES Gas 1 37

TXValeroTexasCity Heater 28 CO Sample #2 10/31/2002 ND 1.00E-01 -2.

YES Gas 1 37

TXValeroTexasCity Heater 28 CO Sample #3 10/31/2002 ND 1.00E-01 -2.

YES Gas 1 38

TXValeroTexasCity Heater 35 CO Sample #1 3/14/2007 ND 1.00E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 38

TXValeroTexasCity Heater 35 CO Sample #2 3/14/2007 ND 1.00E-01 -2.

YES Gas 1 38

TXValeroTexasCity Heater 35 CO Sample #3 3/14/2007 ND 1.00E-01 -2.

YES Gas 1 39

TXValeroTexasCity Heater 44 CO Sample #1 1/6/2000 ND 1.00E-01 -2.

YES Gas 1 39

TXValeroTexasCity Heater 44 CO Sample #2 1/6/2000 ND 1.00E-01 -2.

YES Gas 1 39

TXValeroTexasCity Heater 44 CO Sample #3 1/6/2000 ND 1.00E-01 -2.

YES Gas 1 40

LAWestlakeStyrene 1-90 CO Sample #1 11/10/1992 ND 1.01E-01 -2.

YES Gas 1 40

LAWestlakeStyrene 1-90 CO Sample #2 11/10/1992 ND 1.02E-01 -2.

YES Gas 1 40

LAWestlakeStyrene 1-90 CO Sample #3 11/10/1992 1.00E-01 -2.

YES Gas 1 41

OREvrazOregonSteel

EU-5 Vacuum Degasser Boiler CO Sample #3 4/25/2003 1.02E-01 -2.

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #1 9/12/2000 ND 1.02E-01 -2.

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #1 9/13/2000 ND 1.35E-01 -2.

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #1 9/12/2000 ND 1.02E-01 -2.

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #2 9/12/2000 ND 1.02E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #2 9/13/2000 ND 9.30E-02 -2.

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #3 9/12/2000 ND 1.02E-01 -2.

YES Gas 1 42

LALakeCharlesChemical

LAB-LH-1 (Pacol Charge Heater) CO Sample #3 9/12/2000 5.60E+01 4.

YES Gas 1 43

TXValeroTexasCity Heater 45 CO Sample #1 4/3/2001 ND 1.05E-01 -2.

YES Gas 1 43

TXValeroTexasCity Heater 45 CO Sample #2 4/3/2001 ND 1.09E-01 -2.

YES Gas 1 43

TXValeroTexasCity Heater 45 CO Sample #3 4/3/2001 ND 1.10E-01 -2.

YES Gas 1 44

MSChevronPascagoula F-8400 CO Sample #1 11/7/2007 1.08E-01 -2.

YES Gas 1 44

MSChevronPascagoula F-8400 CO Sample #2 11/7/2007 1.08E-01 -2.

YES Gas 1 44

MSChevronPascagoula F-8400 CO Sample #3 11/7/2007 1.13E-01 -2.

YES Gas 1 45

TXValeroTexasCity Heater 46 CO Sample #1 4/4/2001 ND 1.10E-01 -2.

YES Gas 1 45

TXValeroTexasCity Heater 46 CO Sample #2 4/4/2001 ND 1.09E-01 -2.

YES Gas 1 45

TXValeroTexasCity Heater 46 CO Sample #3 4/4/2001 ND 1.10E-01 -2.

YES Gas 1 46

KYCatlettsburgRefining 2-30-B-1 CO Sample #1 4/23/2004 5.27E-01 -6

YES Gas 1 46

KYCatlettsburgRefining 2-30-B-1 CO Sample #1 8/10/2005 ND 1.14E-01 -2.

YES Gas 1 46

KYCatlettsburgRefining 2-30-B-1 CO Sample #2 8/10/2005 ND 1.17E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 46

KYCatlettsburgRefining 2-30-B-1 CO Sample #3 8/10/2005 ND 1.19E-01 -2.

YES Gas 1 47

LAShellChemicaGeismar

Furnace FS2801 CO Sample #1 2/14/2006 ND 1.01E-01 -2.

YES Gas 1 47

LAShellChemicaGeismar

Furnace FS2801 CO Sample #2 2/14/2006 ND 1.19E-01 -2.

YES Gas 1 47

LAShellChemicaGeismar

Furnace FS2801 CO Sample #3 2/14/2006 ND 1.33E-01 -2.

YES Gas 1 48

KYCatlettsburgRefining 2-23-B-3 CO Sample #1 8/16/2005 ND 1.19E-01 -2.

YES Gas 1 48

KYCatlettsburgRefining 2-23-B-3 CO Sample #2 8/16/2005 ND 1.17E-01 -2.

YES Gas 1 48

KYCatlettsburgRefining 2-23-B-3 CO Sample #3 8/16/2005 ND 1.18E-01 -2.

YES Gas 1 49

TXRohmHaasDeerPark N-13 CO Sample #1 11/8/2006 1.20E-01 -2.

YES Gas 1 49

TXRohmHaasDeerPark N-13 CO Sample #2 11/8/2006 1.20E-01 -2.

YES Gas 1 49

TXRohmHaasDeerPark N-13 CO Sample #3 11/8/2006 1.20E-01 -2.

YES Gas 1 50

TXWesternRefining F-4150 CO Sample #1 8/26/2005 1.22E-01 -2.

YES Gas 1 50

TXWesternRefining F-4150 CO Sample #2 8/26/2005 1.22E-01 -2.

YES Gas 1 50

TXWesternRefining F-4150 CO Sample #3 8/26/2005 1.22E-01 -2.

YES Gas 1 51

TXWesternRefining F-4160 CO Sample #1 8/26/2005 1.22E-01 -2.

YES Gas 1 51

TXWesternRefining F-4160 CO Sample #2 8/26/2005 1.22E-01 -2.

YES Gas 1 51

TXWesternRefining F-4160 CO Sample #3 8/26/2005 1.22E-01 -2.

YES Gas 1 52

TXValeroTexasCity Heater 57 CO Sample #1 1/28/2004 ND 1.27E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 52

TXValeroTexasCity Heater 57 CO Sample #2 1/28/2004 ND 1.28E-01 -2.

YES Gas 1 52

TXValeroTexasCity Heater 57 CO Sample #3 1/28/2004 ND 1.28E-01 -2.

YES Gas 1 53

MSChevronPascagoula F-2440 CO Sample #1 5/15/2007 9.53E-02 -2.

YES Gas 1 53

MSChevronPascagoula F-2440 CO Sample #2 5/15/2007 1.26E-01 -2.

YES Gas 1 53

MSChevronPascagoula F-2440 CO Sample #3 5/15/2007 1.61E-01 -1.

YES Gas 1 54

MSChevronPascagoula F-2450 CO Sample #1 5/15/2007 9.53E-02 -2.

YES Gas 1 54

MSChevronPascagoula F-2450 CO Sample #2 5/15/2007 1.26E-01 -2.

YES Gas 1 54

MSChevronPascagoula F-2450 CO Sample #3 5/15/2007 1.61E-01 -1.

YES Gas 1 55

MSChevronPascagoula F-2460 CO Sample #1 5/15/2007 9.53E-02 -2.

YES Gas 1 55

MSChevronPascagoula F-2460 CO Sample #2 5/15/2007 1.26E-01 -2.

YES Gas 1 55

MSChevronPascagoula F-2460 CO Sample #3 5/15/2007 1.61E-01 -1.

YES Gas 1 56

MSChevronPascagoula F-2470 CO Sample #1 5/15/2007 9.53E-02 -2.

YES Gas 1 56

MSChevronPascagoula F-2470 CO Sample #2 5/15/2007 1.26E-01 -2.

YES Gas 1 56

MSChevronPascagoula F-2470 CO Sample #3 5/15/2007 1.61E-01 -1.

YES Gas 1 57

MSChevronPascagoula F-2480 CO Sample #1 5/15/2007 9.53E-02 -2.

YES Gas 1 57

MSChevronPascagoula F-2480 CO Sample #2 5/15/2007 1.26E-01 -2.

YES Gas 1 57

MSChevronPascagoula F-2480 CO Sample #3 5/15/2007 1.61E-01 -1.

YES Gas 1 58

MSChevronPascagoula F-2490 CO Sample #1 5/15/2007 9.53E-02 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 58

MSChevronPascagoula F-2490 CO Sample #2 5/15/2007 1.26E-01 -2.

YES Gas 1 58

MSChevronPascagoula F-2490 CO Sample #3 5/15/2007 1.61E-01 -1.

YES Gas 1 59

WAConocoPhillipsFerndale 38F-101 CO Sample #1 1/10/2008 ND 1.29E-01 -2.

YES Gas 1 59

WAConocoPhillipsFerndale 38F-101 CO Sample #2 1/10/2008 ND 1.29E-01 -2.

YES Gas 1 59

WAConocoPhillipsFerndale 38F-101 CO Sample #3 1/10/2008 ND 1.29E-01 -2.

YES Gas 1 60

TXValeroTexasCity Heater 58 CO Sample #1 1/29/2004 ND 1.32E-01 -2.

YES Gas 1 60

TXValeroTexasCity Heater 58 CO Sample #2 1/29/2004 ND 1.27E-01 -2.

YES Gas 1 60

TXValeroTexasCity Heater 58 CO Sample #3 1/29/2004 ND 1.27E-01 -2.

YES Gas 1 61

TXRohmHaasDeerPark ACET-2B-1 CO Sample #1 11/14/2006 ND 1.30E-01 -2.

YES Gas 1 61

TXRohmHaasDeerPark ACET-2B-1 CO Sample #1 11/13/2006 1.23E+00 2

YES Gas 1 61

TXRohmHaasDeerPark ACET-2B-1 CO Sample #2 11/13/2006 8.30E-01 -1

YES Gas 1 61

TXRohmHaasDeerPark ACET-2B-1 CO Sample #2 11/14/2006 ND 1.30E-01 -2.

YES Gas 1 61

TXRohmHaasDeerPark ACET-2B-1 CO Sample #3 11/14/2006 ND 1.30E-01 -2.

YES Gas 1 61

TXRohmHaasDeerPark ACET-2B-1 CO Sample #3 11/13/2006 3.30E-01 -1.

YES Gas 1 62

TXValeroTexasCity Heater 18 CO Sample #1 10/15/2002 2.00E-01 -1.

YES Gas 1 62

TXValeroTexasCity Heater 18 CO Sample #2 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 62

TXValeroTexasCity Heater 18 CO Sample #3 10/15/2002 ND 1.00E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 63

TXValeroTexasCity Heater 19 CO Sample #1 10/15/2002 2.00E-01 -1.

YES Gas 1 63

TXValeroTexasCity Heater 19 CO Sample #2 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 63

TXValeroTexasCity Heater 19 CO Sample #3 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 64

TXValeroTexasCity Heater 20 CO Sample #1 10/15/2002 2.00E-01 -1.

YES Gas 1 64

TXValeroTexasCity Heater 20 CO Sample #2 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 64

TXValeroTexasCity Heater 20 CO Sample #3 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 65

TXValeroTexasCity Heater 21 CO Sample #1 10/15/2002 2.00E-01 -1.

YES Gas 1 65

TXValeroTexasCity Heater 21 CO Sample #2 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 65

TXValeroTexasCity Heater 21 CO Sample #3 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 66

TXValeroTexasCity Heater 22 CO Sample #1 10/15/2002 2.00E-01 -1.

YES Gas 1 66

TXValeroTexasCity Heater 22 CO Sample #2 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 66

TXValeroTexasCity Heater 22 CO Sample #3 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 67

TXValeroTexasCity Heater 23 CO Sample #1 10/15/2002 2.00E-01 -1.

YES Gas 1 67

TXValeroTexasCity Heater 23 CO Sample #2 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 67

TXValeroTexasCity Heater 23 CO Sample #3 10/15/2002 ND 1.00E-01 -2.

YES Gas 1 68

TXWesternRefining H-8801 CO Sample #1 5/16/2007 1.00E-01 -2.

YES Gas 1 68

TXWesternRefining H-8801 CO Sample #2 5/16/2007 7.00E-02 -2.

YES Gas 1 68

TXWesternRefining H-8801 CO Sample #3 5/16/2007 2.30E-01 -1.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 69

TXWesternRefining H-8802 CO Sample #1 5/16/2007 1.00E-01 -2.

YES Gas 1 69

TXWesternRefining H-8802 CO Sample #2 5/16/2007 7.00E-02 -2.

YES Gas 1 69

TXWesternRefining H-8802 CO Sample #3 5/16/2007 2.30E-01 -1.

YES Gas 1 70

IAADMClinton

EUCOG-5 #2 Gas Fired Boiler CO Sample #2 3/7/2008 1.35E-01 -2.

YES Gas 1 70

IAADMClinton

EUCOG-5 #2 Gas Fired Boiler CO Sample #3 3/10/2008 1.35E-01 -2.

YES Gas 1 71

TXDeerParkRefinery H31003 CO Sample #1 5/25/2001 ND 1.35E-01 -2.

YES Gas 1 71

TXDeerParkRefinery H31003 CO Sample #2 5/25/2001 ND 1.35E-01 -2.

YES Gas 1 71

TXDeerParkRefinery H31003 CO Sample #3 5/25/2001 ND 1.35E-01 -2.

YES Gas 1 72

TXDeerParkRefinery H5104 CO Sample #1 5/23/2001 ND 1.35E-01 -2.

YES Gas 1 72

TXDeerParkRefinery H5104 CO Sample #2 5/23/2001 ND 1.35E-01 -2.

YES Gas 1 72

TXDeerParkRefinery H5104 CO Sample #3 5/23/2001 ND 1.35E-01 -2.

YES Gas 1 73

TXLyondellPasadena B-1751 CO Sample #1 1/26/2007 1.35E-01 -2.

YES Gas 1 73

TXLyondellPasadena B-1751 CO Sample #2 1/26/2007 1.35E-01 -2.

YES Gas 1 73

TXLyondellPasadena B-1751 CO Sample #3 1/26/2007 1.35E-01 -2.

YES Gas 1 74

TXLyondellPasadena B-2890 CO Sample #1 1/24/2007 1.35E-01 -2.

YES Gas 1 74

TXLyondellPasadena B-2890 CO Sample #2 1/24/2007 1.35E-01 -2.

YES Gas 1 74

TXLyondellPasadena B-2890 CO Sample #3 1/24/2007 1.35E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 75

TXLyondellPasadena B-801 CO Sample #1 3/22/2007 1.35E-01 -2.

YES Gas 1 75

TXLyondellPasadena B-801 CO Sample #2 3/22/2007 1.35E-01 -2.

YES Gas 1 75

TXLyondellPasadena B-801 CO Sample #3 3/22/2007 1.35E-01 -2.

YES Gas 1 76

TXWesternRefining F-1602 CO Sample #1 8/25/2005 1.35E-01 -2.

YES Gas 1 76

TXWesternRefining F-1602 CO Sample #2 8/25/2005 1.35E-01 -2.

YES Gas 1 76

TXWesternRefining F-1602 CO Sample #3 8/25/2005 1.35E-01 -2.

YES Gas 1 77

TXRohmHaasDeerPark HT-49 CO Sample #1 12/6/2006 ND 1.40E-01 -1.

YES Gas 1 77

TXRohmHaasDeerPark HT-49 CO Sample #2 12/6/2006 ND 1.40E-01 -1.

YES Gas 1 78

TXRohmHaasDeerPark N-12 CO Sample #1 11/7/2006 1.40E-01 -1.

YES Gas 1 78

TXRohmHaasDeerPark N-12 CO Sample #2 11/7/2006 1.30E-01 -2.

YES Gas 1 78

TXRohmHaasDeerPark N-12 CO Sample #3 11/7/2006 1.50E-01 -1.

YES Gas 1 79

LAShellChemicaGeismar

Furnace FS801 CO Sample #1 2/15/2006 ND 1.35E-01 -2.

YES Gas 1 79

LAShellChemicaGeismar

Furnace FS801 CO Sample #2 2/15/2006 ND 1.43E-01 -1.

YES Gas 1 79

LAShellChemicaGeismar

Furnace FS801 CO Sample #3 2/15/2006 ND 1.43E-01 -1.

YES Gas 1 80

DEDuPontEdgemoor RX-9 CO Sample #1 6/28/2007 ND 1.05E-01 -2.

YES Gas 1 80

DEDuPontEdgemoor RX-9 CO Sample #2 6/28/2007 1.05E-01 -2.

YES Gas 1 80

DEDuPontEdgemoor RX-9 CO Sample #3 6/28/2007 2.11E-01 -1.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 81

PANorfolkSouthern Boiler 1 CO Sample #1 10/19/2006 4.56E+00 1.

YES Gas 1 81

PANorfolkSouthern Boiler 1 CO Sample #2 10/19/2006 2.53E+00 9

YES Gas 1 81

PANorfolkSouthern Boiler 1 CO Sample #2 10/19/2006 8.00E-02 -2.

YES Gas 1 81

PANorfolkSouthern Boiler 1 CO Sample #3 10/19/2006 1.50E-01 -1.

YES Gas 1 81

PANorfolkSouthern Boiler 1 CO Sample #3 10/19/2006 1.08E+00 7

YES Gas 1 81

PANorfolkSouthern Boiler 1 CO Sample #3 10/19/2006 2.58E+00 9

YES Gas 1 82

TXWesternRefining 109 CO Sample #1 2/28/2006 4.59E-02 -3.

YES Gas 1 82

TXWesternRefining 109 CO Sample #2 2/28/2006 1.95E-01 -1.

YES Gas 1 82

TXWesternRefining 109 CO Sample #3 2/28/2006 2.31E-01 -1.

YES Gas 1 83

TXRohmHaasDeerPark ACET-2A-1 CO Sample #1 11/14/2006 1.70E-01 -1.

YES Gas 1 83

TXRohmHaasDeerPark ACET-2A-1 CO Sample #1 11/13/2006 4.71E+00 1.

YES Gas 1 83

TXRohmHaasDeerPark ACET-2A-1 CO Sample #2 11/14/2006 1.50E-01 -1.

YES Gas 1 83

TXRohmHaasDeerPark ACET-2A-1 CO Sample #2 11/13/2006 7.42E+00 2.

YES Gas 1 83

TXRohmHaasDeerPark ACET-2A-1 CO Sample #3 11/14/2006 1.80E-01 -1.

YES Gas 1 83

TXRohmHaasDeerPark ACET-2A-1 CO Sample #3 11/13/2006 6.56E+00 1.

YES Gas 1 84

TXValeroCorpusChristi 154-H-1 CO Sample #1 5/20/2008 ND 1.00E-01 -2.

YES Gas 1 84

TXValeroCorpusChristi 154-H-1 CO Sample #2 5/20/2008 2.00E-01 -1.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 84

TXValeroCorpusChristi 154-H-1 CO Sample #3 5/20/2008 2.00E-01 -1.

YES Gas 1 85

MSChevronPascagoula F-6410 CO Sample #1 12/6/2007 6.27E-02 -2.

YES Gas 1 85

MSChevronPascagoula F-6410 CO Sample #2 12/6/2007 6.33E-02 -2.

YES Gas 1 85

MSChevronPascagoula F-6410 CO Sample #3 12/6/2007 3.78E-01 -9

YES Gas 1 86

KYCatlettsburgRefining 2-36-B-1 CO Sample #1 9/14/2005 ND 1.69E-01 -1.

YES Gas 1 86

KYCatlettsburgRefining 2-36-B-1 CO Sample #1 6/23/2004 ND 3.12E+00 1.

YES Gas 1 86

KYCatlettsburgRefining 2-36-B-1 CO Sample #2 6/23/2004 ND 3.14E+00 1.

YES Gas 1 86

KYCatlettsburgRefining 2-36-B-1 CO Sample #2 9/14/2005 ND 1.69E-01 -1.

YES Gas 1 86

KYCatlettsburgRefining 2-36-B-1 CO Sample #3 9/14/2005 ND 1.69E-01 -1.

YES Gas 1 86

KYCatlettsburgRefining 2-36-B-1 CO Sample #3 6/23/2004 ND 3.17E+00 1.

YES Gas 1 87

OKConocoPhillipsPoncaCity H-0048 CO Sample #1 4/7/2005 2.20E-01 -1.

YES Gas 1 87

OKConocoPhillipsPoncaCity H-0048 CO Sample #2 4/7/2005 1.60E-01 -1.

YES Gas 1 87

OKConocoPhillipsPoncaCity H-0048 CO Sample #3 4/7/2005 1.30E-01 -2.

YES Gas 1 88

MTMontanaRefining

H-1801 Hydrogen Plant Heater CO Sample #1 9/20/2007 1.71E-01 -1.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 88

MTMontanaRefining

H-1801 Hydrogen Plant Heater CO Sample #2 9/20/2007 8.57E-02 -2.

YES Gas 1 88

MTMontanaRefining

H-1801 Hydrogen Plant Heater CO Sample #3 9/20/2007 2.57E-01 -1.

YES Gas 1 89

TXRohmHaasDeerPark ACET-2A-3 CO Sample #1 11/28/2006 4.00E-01 -9

YES Gas 1 89

TXRohmHaasDeerPark ACET-2A-3 CO Sample #1 11/27/2006 3.70E-01 -9

YES Gas 1 89

TXRohmHaasDeerPark ACET-2A-3 CO Sample #2 11/28/2006 4.30E-01 -8

YES Gas 1 89

TXRohmHaasDeerPark ACET-2A-3 CO Sample #2 11/27/2006 8.00E-02 -2.

YES Gas 1 89

TXRohmHaasDeerPark ACET-2A-3 CO Sample #3 11/27/2006 8.00E-02 -2.

YES Gas 1 89

TXRohmHaasDeerPark ACET-2A-3 CO Sample #3 11/28/2006 3.40E-01 -1.

YES Gas 1 90

MSChevronPascagoula F-8300B CO Sample #1 3/2/2007 7.88E-02 -2.

YES Gas 1 90

MSChevronPascagoula F-8300B CO Sample #2 3/2/2007 7.90E-02 -2.

YES Gas 1 90

MSChevronPascagoula F-8300B CO Sample #3 3/2/2007 3.96E-01 -9

YES Gas 1 91

VAUniversityofVirginia 7103-1-01R CO Sample #1 12/5/2007 2.60E-01 -1.

YES Gas 1 91

VAUniversityofVirginia 7103-1-01R CO Sample #2 12/5/2007 1.30E-01 -2.

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-1 8/12/2009 5.68E-01 -5

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-3 8/13/2009 1.48E-01 -1.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-4 8/13/2009 4.36E-01 -8

YES Gas 1 yes 1

CORockyMtnSteel212

Rod/Bar Mill Furnace 95OPPB088 CO M10-6 8/14/2009 8.59E-01 -1

YES Gas 1 yes 2

MDSeverstalSparrows

CRM Batch Annealing Furnaces CO Sample #1 7/18/2000 ND 1.35E+00 3

YES Gas 1 yes 2

MDSeverstalSparrows

CRM Batch Annealing Furnaces CO Sample #2 7/18/2000 ND 1.35E+00 3

YES Gas 1 yes 2

MDSeverstalSparrows

CRM Batch Annealing Furnaces CO Sample #3 7/19/2000 ND 1.35E+00 3

YES Gas 2 1

TXEquistarChemicals UTBLRG CO Sample #1 2/28/2006 2.23E-02 -3.

YES Gas 2 1

TXEquistarChemicals UTBLRG CO Sample #2 2/28/2006 2.07E-02 -3.

YES Gas 2 1

TXEquistarChemicals UTBLRG CO Sample #3 2/28/2006 2.04E-02 -3.

YES Gas 2 2

TXFlintHillsPortArthur

LOUBOILER10 CO Sample #1 6/10/1998 ND 1.00E-01 -2.

YES Gas 2 2

TXFlintHillsPortArthur

LOUBOILER10 CO Sample #2 6/10/1998 4.00E-02 -3.

YES Gas 2 2

TXFlintHillsPortArthur

LOUBOILER10 CO Sample #3 6/10/1998 ND 1.00E-01 -2.

YES Gas 2 3

TXEquistarChannelview F38001A CO Sample #1 2/16/2004 ND 1.00E-01 -2.

YES Gas 2 3

TXEquistarChannelview F38001A CO Sample #2 2/16/2004 ND 1.00E-01 -2.

YES Gas 2 3

TXEquistarChannelview F38001A CO Sample #3 2/16/2004 ND 1.00E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 2 4

TXEquistarChannelview F38001B CO Sample #1 2/16/2004 ND 1.00E-01 -2.

YES Gas 2 4

TXEquistarChannelview F38001B CO Sample #2 2/16/2004 ND 1.00E-01 -2.

YES Gas 2 4

TXEquistarChannelview F38001B CO Sample #3 2/16/2004 ND 1.00E-01 -2.

YES Gas 2 5

TXFlintHillsPortArthur

LOUBOILER9 CO Sample #1 6/9/1998 ND 1.00E-01 -2.

YES Gas 2 5

TXFlintHillsPortArthur

LOUBOILER9 CO Sample #2 6/9/1998 ND 1.00E-01 -2.

YES Gas 2 5

TXFlintHillsPortArthur

LOUBOILER9 CO Sample #3 6/9/1998 ND 1.00E-01 -2.

YES Gas 2 6

TXLyondellChannelview F6101 CO Sample #1 8/7/2002 ND 1.00E-01 -2.

YES Gas 2 6

TXLyondellChannelview F6101 CO Sample #2 8/7/2002 ND 1.00E-01 -2.

YES Gas 2 6

TXLyondellChannelview F6101 CO Sample #3 8/7/2002 ND 1.00E-01 -2.

YES Gas 2 7

TXLyondellChannelview F6105 CO Sample #1 8/8/2002 ND 1.00E-01 -2.

YES Gas 2 7

TXLyondellChannelview F6105 CO Sample #2 8/8/2002 ND 1.00E-01 -2.

YES Gas 2 7

TXLyondellChannelview F6105 CO Sample #3 8/8/2002 ND 1.00E-01 -2.

YES Gas 2 8

TXEquistarChannelview F4601 CO Sample #1 2/13/2007 ND 1.10E-01 -2.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Gas 2 8

TXEquistarChannelview F4601 CO Sample #2 2/13/2007 ND 1.10E-01 -2.

YES Gas 2 8

TXEquistarChannelview F4601 CO Sample #3 2/13/2007 ND 1.10E-01 -2.

YES Gas 2 9

TXLyondellChannelview F6103 CO Sample #1 2/26/2007 ND 1.10E-01 -2.

YES Gas 2 9

TXLyondellChannelview F6103 CO Sample #2 2/26/2007 ND 1.10E-01 -2.

YES Gas 2 9

TXLyondellChannelview F6103 CO Sample #3 2/26/2007 ND 1.10E-01 -2.

YES Liquid 1

SCDAKAmericas P8F CO Sample #4 7/15/2009 6.43E-02 -2.

YES Liquid 1

SCDAKAmericas P8F CO Sample #5 7/15/2009 3.86E-02 -3.

YES Liquid 2

ORGeorgiaPacificWaunaMill

EU33 - Power Boiler CO Sample #1 3/14/2007 ND 1.25E-01 -2.

YES Liquid 2

ORGeorgiaPacificWaunaMill

EU33 - Power Boiler CO Sample #2 3/14/2007 ND 1.25E-01 -2.

YES Liquid 2

ORGeorgiaPacificWaunaMill

EU33 - Power Boiler CO Sample #3 3/14/2007 ND 1.25E-01 -2.

YES Liquid 3

NJSunocoWestville Boiler #8 CO Sample #1 11/20/2007 ND 1.28E-01 -2.

YES Liquid 3

NJSunocoWestville Boiler #8 CO Sample #2 11/20/2007 ND 1.28E-01 -2.

YES Liquid 3

NJSunocoWestville Boiler #8 CO Sample #3 11/20/2007 ND 1.28E-01 -2.

YES Liquid 4

NJSunocoWestville Boiler #7 CO Sample #1 12/19/2005 3.86E-02 -3.
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Liquid 4

NJSunocoWestville Boiler #7 CO Sample #2 12/19/2005 2.83E-01 -1.

YES Liquid 4

NJSunocoWestville Boiler #7 CO Sample #3 12/19/2005 2.70E-01 -1.

YES Liquid 5

NENebraskaCityStation

Auxiliary Boiler 2 CO Sample #1 6/6/2007 2.80E-01 -1.

YES Liquid 5

NENebraskaCityStation

Auxiliary Boiler 2 CO Sample #2 6/6/2007 2.10E-01 -1.

YES Liquid 5

NENebraskaCityStation

Auxiliary Boiler 2 CO Sample #3 6/6/2007 3.30E-01 -1.

YES Liquid 6

NJSunocoWestville Boiler #5 CO Sample #1 11/16/2007 3.85E-01 -9

YES Liquid 6

NJSunocoWestville Boiler #5 CO Sample #2 11/16/2007 2.57E-01 -1.

YES Liquid 6

NJSunocoWestville Boiler #5 CO Sample #3 11/16/2007 2.57E-01 -1.

YES Liquid 7

SCGPChemRussellville FO Boiler CO Sample #1 8/25/2009 1.03E-01 -2.

YES Liquid 7

SCGPChemRussellville FO Boiler CO Sample #2 8/25/2009 7.72E-02 -2.

YES Liquid 7

SCGPChemRussellville FO Boiler CO Sample #3 8/25/2009 9.39E-01 -6

YES Liquid 8

NJMerckRahway

E750009 - Boiler #9 CO Sample #1 3/14/2008 ND 5.15E-01 -6

YES Liquid 8

NJMerckRahway

E750009 - Boiler #9 CO Sample #2 3/14/2008 ND 5.15E-01 -6

YES Liquid 8

NJMerckRahway

E750009 - Boiler #9 CO Sample #3 3/14/2008 ND 5.15E-01 -6

YES Liquid 9

OHOSUColumbus B140 CO Sample #1 2/2/2005 ND 5.19E-01 -6

YES Liquid 9

OHOSUColumbus B140 CO Sample #2 2/2/2005 5.93E-01 -5

YES Liquid 9

OHOSUColumbus B140 CO Sample #3 2/2/2005 ND 5.21E-01 -6

YES Liquid 10

NCCampLejeuneMCB

C-CG-650-84B CO Sample #1 3/18/2008 7.00E-01 -3
Appendix G-11: Ranked Existing Unit Performance by Fuel under Alternative Solid Waste Definition

Test 

Data in 

Top 

12pct

MACT Floor 

FuelCat

Metal 

Furnace? Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under 

Alt Defn?

ppm @ 3% 

O2

ln (

3% 

YES Liquid 10

NCCampLejeuneMCB

C-CG-650-84B CO Sample #2 3/18/2008 8.00E-01 -2

YES Liquid 10

NCCampLejeuneMCB

C-CG-650-84B CO Sample #3 3/18/2008 2.00E-01 -1.

YES Liquid 11

VADominionPossumPoint

Aux. Boiler 001 CO Sample #1 3/11/2008 3.95E-01 -9

YES Liquid 11

VADominionPossumPoint

Aux. Boiler 001 CO Sample #2 3/11/2008 7.71E-01 -2

YES Liquid 11

VADominionPossumPoint

Aux. Boiler 001 CO Sample #3 3/11/2008 7.20E-01 -3

YES Liquid 12

PAKeystonePowerPlantShelocta Aux Boiler A CO Sample #1 6/22/1993 3.03E-01 -1.

YES Liquid 12

PAKeystonePowerPlantShelocta Aux Boiler A CO Sample #2 6/22/1993 1.22E+00 1

YES Liquid 13

NJSunocoWestville Boiler #6 CO Sample #1 11/15/2007 8.98E-01 -1

YES Liquid 13

NJSunocoWestville Boiler #6 CO Sample #2 11/15/2007 7.70E-01 -2

YES Liquid 13

NJSunocoWestville Boiler #6 CO Sample #3 11/15/2007 8.98E-01 -1
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 1/25/2007 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 11/15/2002 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 2/8/1999 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 1/5/2001 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 2/4/2005 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 12/17/1999 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 1/31/2000 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 12/30/2003 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 1/24/2008 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 5/3/2005 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 1/9/2002 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #1 1/5/2006 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 1/31/2000 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 12/30/2003 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 1/5/2001 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 5/3/2005 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 1/25/2007 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 12/17/1999 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 1/5/2006 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 11/15/2002 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 2/8/1999 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 1/9/2002 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 2/4/2005 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #2 1/24/2008 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 1/31/2000 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 12/30/2003 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 5/5/2005 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 1/9/2002 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 11/15/2002 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 1/24/2008 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 1/5/2001 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 2/4/2005 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 1/25/2007 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 12/17/1999 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 2/8/1999 

YES Biomass

Dutch Oven/Susp. Burner 1

FLUSSugarCorp Boiler No. 7 CO Sample #3 1/5/2006 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #1 8/11/2009 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #1 6/22/2006 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #1 8/11/2009 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #2 8/11/2009 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #2 6/22/2006 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #2 8/11/2009 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #3 6/22/2006 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #3 8/12/2009 

YES Biomass

Dutch Oven/Susp. Burner 2

WAGraysHarborPaper

No. 6 Boiler (EU2) CO Sample #3 8/12/2009 

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) CO 1 8/27/2009 

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) CO 2 8/29/2009 

YES Biomass FB 1

NDCargillWestFargo

Foster Wheeler Boiler (EU43) CO 3 8/29/2009 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #1 6/18/2008 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #1 6/19/2008 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #2 6/18/2008 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #2 6/18/2008 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #2 6/19/2008 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #3 6/19/2008 

YES Biomass Fuel Cell 1

KYWeyerhaeuserEKY MP 01-01 CO Sample #3 6/18/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #1 6/18/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #1 6/19/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #2 6/19/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #2 6/18/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #2 6/18/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #3 6/19/2008 

YES Biomass Fuel Cell 2

KYWeyerhaeuserEKY MP 01-03 CO Sample #3 6/18/2008 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 8/11/2009 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 9/28/2004 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 7/17/2009 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #1 12/3/2003 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 7/17/2009 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 8/12/2009 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 12/3/2003 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #2 9/28/2004 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 9/28/2004 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 8/12/2009 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 7/20/2009 

YES Biomass Fuel Cell 3

ARWeyerhaeuserDierksMill SN-45 CO Sample #3 12/3/2003 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #1 9/18/1996 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #1 8/12/2009 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #1 11/10/2004 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #2 11/10/2004 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #2 9/18/1996 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #2 8/13/2009 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #3 9/18/1996 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #3 8/13/2009 

YES Biomass Fuel Cell 4

WAWeyerhaeuser_Raymond

Hog Fuel Boiler EU1 CO Sample #3 11/10/2004 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #1 6/28/2005 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #1 8/31/2007 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #1 8/4/2009 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #1 8/22/2003 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #1 7/11/2003 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #1 8/23/1999 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #2 8/4/2009 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #2 6/28/2005 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #2 8/23/1999 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #2 7/11/2003 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #2 8/22/2003 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #2 8/31/2007 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #3 8/4/2009 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #3 8/23/1999 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #3 8/22/2003 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #3 6/28/2005 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #3 8/31/2007 

YES Biomass Fuel Cell 5

MSWeyerhaeuserBruce

AA-002 No. 2 Boiler CO Sample #3 7/11/2003 

YES Biomass

Stoker/SlopedGrate/Other 1

IDChilcoLakeSawmill HFB1 CO Sample #1 3/30/2005 

YES Biomass

Stoker/SlopedGrate/Other 1

IDChilcoLakeSawmill HFB1 CO Sample #2 3/30/2005 

YES Biomass

Stoker/SlopedGrate/Other 1

IDChilcoLakeSawmill HFB1 CO Sample #3 3/30/2005 

YES Biomass

Stoker/SlopedGrate/Other 2

ARWestFraserHuttig SN-24 CO Sample #1 3/1/2005 

YES Biomass

Stoker/SlopedGrate/Other 2

ARWestFraserHuttig SN-24 CO Sample #2 3/1/2005 

YES Biomass

Stoker/SlopedGrate/Other 2

ARWestFraserHuttig SN-24 CO Sample #3 3/1/2005 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Stoker/SlopedGrate/Other 3

MILPCSagola TOH-Wood CO Sample #1 3/12/2008 

YES Biomass

Stoker/SlopedGrate/Other 3

MILPCSagola TOH-Wood CO Sample #2 3/12/2008 

YES Biomass

Stoker/SlopedGrate/Other 3

MILPCSagola TOH-Wood CO Sample #3 3/12/2008 

YES Biomass

Stoker/SlopedGrate/Other 4

INConsolidatedGrainandBarge P17B CO Sample #1 3/5/2008 

YES Biomass

Stoker/SlopedGrate/Other 4

INConsolidatedGrainandBarge P17B CO Sample #2 3/5/2008 

YES Biomass

Stoker/SlopedGrate/Other 4

INConsolidatedGrainandBarge P17B CO Sample #3 3/5/2008 

YES Biomass

Stoker/SlopedGrate/Other 5

INConsolidatedGrainandBarge P17C CO Sample #1 3/5/2008 

YES Biomass

Stoker/SlopedGrate/Other 5

INConsolidatedGrainandBarge P17C CO Sample #2 3/5/2008 

YES Biomass

Stoker/SlopedGrate/Other 5

INConsolidatedGrainandBarge P17C CO Sample #3 3/5/2008 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #1 4/23/2008 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #1 4/22/2008 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #1 6/16/2007 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #2 6/16/2007 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #2 4/23/2008 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #2 4/22/2008 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #3 4/22/2008 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #3 6/16/2007 

YES Biomass

Stoker/SlopedGrate/Other 6

MNAndersonCorpBayport

Boiler 11 EU620 CO Sample #3 4/23/2008 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #1 4/23/2008 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #1 4/22/2008 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #1 6/16/2007 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #2 6/16/2007 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #2 4/22/2008 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #2 4/23/2008 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #3 4/23/2008 

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #3 4/22/2008 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Biomass

Stoker/SlopedGrate/Other 7

MNAndersonCorpBayport

Boiler 12 EU621 CO Sample #3 6/16/2007 

YES Biomass

Stoker/SlopedGrate/Other 8

MSGPNewAugusta

AA-015 Power Boiler CO Sample #1 9/12/2007 

YES Biomass

Stoker/SlopedGrate/Other 8

MSGPNewAugusta

AA-015 Power Boiler CO Sample #2 9/12/2007 

YES Biomass

Stoker/SlopedGrate/Other 8

MSGPNewAugusta

AA-015 Power Boiler CO Sample #3 9/12/2007 

YES Biomass

Stoker/SlopedGrate/Other 9

ALMeadwestvacoCottonton46

No.3 Wood Residue Boiler CO Sample #1 11/1/2007 

YES Biomass

Stoker/SlopedGrate/Other 9

ALMeadwestvacoCottonton46

No.3 Wood Residue Boiler CO Sample #2 11/1/2007 

YES Biomass

Stoker/SlopedGrate/Other 9

ALMeadwestvacoCottonton46

No.3 Wood Residue Boiler CO Sample #3 11/1/2007 

YES Coal FB 1

IAADMCornProcessingCR EU-530 CO Sample #1 11/20/2002 

YES Coal FB 1

IAADMCornProcessingCR EU-530 CO Sample #2 11/20/2002 

YES Coal FB 1

IAADMCornProcessingCR EU-530 CO Sample #3 11/20/2002 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #1 8/11/2009 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #1 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #1 5/15/1989 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #2 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #2 5/15/1989 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #2 8/11/2009 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #3 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #3 8/12/2009 

YES Coal FB 2

IAADMCornProcessingCR EU-501B CO Sample #3 5/15/1989 

YES Coal FB 3

IAADMCornProcessingCR EU-502A CO Sample #1 5/19/1989 

YES Coal FB 3

IAADMCornProcessingCR EU-502A CO Sample #2 5/19/1989 

YES Coal FB 3

IAADMCornProcessingCR EU-502A CO Sample #3 5/19/1989 

YES Coal FB 4

IAADMCornProcessingCR EU-501A CO Sample #1 5/25/1989 

YES Coal FB 4

IAADMCornProcessingCR EU-501A CO Sample #2 5/25/1989 

YES Coal FB 4

IAADMCornProcessingCR EU-501A CO Sample #3 5/26/1989 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO 1 7/21/2009 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO 2 7/21/2009 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO 3 7/22/2009 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO 4 7/22/2009 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO 5 7/23/2009 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO 6 7/23/2009 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO Sample #1 11/29/2006 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO Sample #2 11/29/2006 

YES Coal FB 5

INPurdueUniverisity Boiler 5 CO Sample #3 11/29/2006 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #1 3/30/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #1 3/29/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #1 3/29/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #2 3/29/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #2 3/29/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #2 3/30/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #3 3/29/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #3 3/29/2007 

YES Coal PC 1

ILDukeEnergyTuscola Unit 3 CO Sample #3 3/30/2007 

YES Coal PC 2

ILDukeEnergyTuscola Unit 4 CO Sample #1 3/30/2007 

YES Coal PC 2

ILDukeEnergyTuscola Unit 4 CO Sample #2 3/30/2007 

YES Coal PC 2

ILDukeEnergyTuscola Unit 4 CO Sample #3 3/30/2007 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #1 3/29/2007 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #1 3/29/2007 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #2 3/29/2007 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #2 3/29/2007 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #3 3/29/2007 

YES Coal PC 3

ILDukeEnergyTuscola Unit 1 CO Sample #3 3/29/2007 

YES Coal PC 4

VAPhilipMorrisPark500 B2 CO Sample #1 9/21/2005 

YES Coal PC 4

VAPhilipMorrisPark500 B2 CO Sample #2 9/21/2005 

YES Coal PC 4

VAPhilipMorrisPark500 B2 CO Sample #3 9/21/2005 

YES Coal PC 5

AZCatalystPaperSnowflake

Power Boiler #2 Coal CO Sample #1 3/24/2006 

YES Coal PC 5

AZCatalystPaperSnowflake

Power Boiler #2 Coal CO Sample #2 3/24/2006 

YES Coal PC 5

AZCatalystPaperSnowflake

Power Boiler #2 Coal CO Sample #3 3/24/2006 

YES Coal

Stoker/SlopedGrate/Other 1

INNotreDame B-4 CO Sample #1 8/25/2009 

YES Coal

Stoker/SlopedGrate/Other 1

INNotreDame B-4 CO Sample #2 8/25/2009 

YES Coal

Stoker/SlopedGrate/Other 1

INNotreDame B-4 CO Sample #3 8/25/2009 

YES Coal

Stoker/SlopedGrate/Other 2

OHMortonSaltRittman

B002 - CoalFired Boiler #2 CO 1 8/25/2009 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Coal

Stoker/SlopedGrate/Other 2

OHMortonSaltRittman

B002 - CoalFired Boiler #2 CO 2 8/26/2009 

YES Coal

Stoker/SlopedGrate/Other 2

OHMortonSaltRittman

B002 - CoalFired Boiler #2 CO 3 8/27/2009 

YES Coal

Stoker/SlopedGrate/Other 3

WVDuPontWashingtonWorks P05 CO Sample #1 11/2/2005 

YES Coal

Stoker/SlopedGrate/Other 3

WVDuPontWashingtonWorks P05 CO Sample #2 11/2/2005 

YES Coal

Stoker/SlopedGrate/Other 3

WVDuPontWashingtonWorks P05 CO Sample #3 11/3/2005 

YES Coal

Stoker/SlopedGrate/Other 4

OHAppletonIdeas

Boiler 4 (B003) CO Sample #1 1/29/2003 

YES Coal

Stoker/SlopedGrate/Other 4

OHAppletonIdeas

Boiler 4 (B003) CO Sample #2 1/29/2003 

YES Coal

Stoker/SlopedGrate/Other 4

OHAppletonIdeas

Boiler 4 (B003) CO Sample #3 1/29/2003 

YES Coal

Stoker/SlopedGrate/Other 5

OHAkronThermalEnergy

Boiler #32 (B001) CO Sample #1 3/1/2007 

YES Coal

Stoker/SlopedGrate/Other 5

OHAkronThermalEnergy

Boiler #32 (B001) CO Sample #2 3/1/2007 

YES Coal

Stoker/SlopedGrate/Other 5

OHAkronThermalEnergy

Boiler #32 (B001) CO Sample #3 3/1/2007 

YES Coal

Stoker/SlopedGrate/Other 6

PABellefieldPlant Boiler 1 CO Sample #1 6/6/2006 

YES Coal

Stoker/SlopedGrate/Other 6

PABellefieldPlant Boiler 1 CO Sample #2 6/6/2006 
Appendix G-12: Ranked Existing Unit Performance by Fuel and Combustor Design under Alternative Solid Was

Test Data in 

Top 12pct

MACT Floor 

FuelCat

Combustor 

Design Rank FacilityID

CombustorID

_common

Pollutant_Na

me TestID

TestDate_co

mmon

NonDetect?

Test Burning 

Waste under Alt 

Defn?

YES Coal

Stoker/SlopedGrate/Other 6

PABellefieldPlant Boiler 1 CO Sample #3 6/6/2006 
Appendix G-13: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Biomass

No. of sources = 108 108

No. in MACT floor = 13 13

Avge of top 12% = 5.89E-03 -5.68E+00

Std Deviation of top 12% = 6.25E-03 1.13E+00

Skewness = 1.97 -0.27

Kurtosis = 4.65 -0.52

SE Skewness 0.22 0.22

Skewness Test non-normal normal

SE Kurtosis 0.43 0.43

Kurtosis Test non-normal normal

Number of test runs = 129 129

Number of test runs that contained non-detect 

values

2 2

Highest test run = 3.55E-02 -3.34E+00

99% t-statistic for UPL 2.36E+00 2.36E+00

99% UPL of top 12% (test runs) = 1.45E-02 1.61E-02

Coal

No. of sources = 335 335

No. in MACT floor = 41 41

Avge of top 12% = 8.66E-03 -5.62E+00

Std Deviation of top 12% = 1.64E-02 1.28E+00

Skewness = 4.84 0.19

Kurtosis = 32.35 0.45

SE Skewness 0.16 0.16

Skewness Test non-normal normal

SE Kurtosis 0.31 0.31

Kurtosis Test non-normal normal

Number of test runs = 242 242

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.56E-01 -1.86E+00

99% t-statistic for UPL 2.34E+00 2.34E+00

99% UPL of top 12% (test runs) = 3.09E-02 2.06E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-13: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Liquid

No. of sources = 81 81

No. in MACT floor = 10 10

Avge of top 12% = 1.29E-03 -6.87E+00

Std Deviation of top 12% = 8.55E-04 7.54E-01

Skewness = 1.84 -1.15

Kurtosis = 5.82 2.84

SE Skewness 0.45 0.45

Skewness Test non-normal normal

SE Kurtosis 0.89 0.89

Kurtosis Test non-normal non-normal

Number of test runs = 30 30

Number of test runs that contained non-detect 

values

1 1

Highest test run = 4.51E-03 -5.40E+00

99% t-statistic for UPL 2.46E+00 2.46E+00

99% UPL of top 12% (test runs) = 2.57E-03 3.18E-03

Gas 1 Excluding Metallurgical Furnaces

No. of sources = 143 143

No. in MACT floor = 18 18

Avge of top 12% = 3.88E-03 -7.45E+00

Std Deviation of top 12% = 1.45E-02 1.48E+00

Skewness = 6.14 1.69

Kurtosis = 42.28 2.99

SE Skewness 0.30 0.30

Skewness Test non-normal non-normal

SE Kurtosis 0.60 0.60

Kurtosis Test non-normal non-normal

Number of test runs = 66 66

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.08E-01 -2.23E+00

99% t-statistic for UPL 2.39E+00 2.39E+00

99% UPL of top 12% (test runs) = 2.42E-02 4.67E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-13: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Gas 1 - Metallurgical Furnaces

No. of sources = 9 9

No. in MACT floor = 2 2

Avge of top 12% = 4.70E-03 -7.84E+00

Std Deviation of top 12% = 6.45E-03 3.50E+00

Skewness = 1.00 -0.49

Kurtosis = -1.03 -1.70

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.53E-02 -4.18E+00

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 1.72E-02 3.41E-01

Gas 2

No. of sources = 13 13

No. in MACT floor = 2 2

Avge of top 12% = 1.10E-02 -5.24E+00

Std Deviation of top 12% = 1.15E-02 1.45E+00

Skewness = 1.23 -0.61

Kurtosis = 0.71 -0.39

SE Skewness 0.43 0.43

Skewness Test non-normal normal

SE Kurtosis 0.85 0.85

Kurtosis Test normal normal

Number of test runs = 33 33

Number of test runs that contained non-detect 

values

0 0

Highest test run = 4.21E-02 -3.17E+00

99% t-statistic for UPL 2.45E+00 2.45E+00

99% UPL of top 12% (test runs) = 2.79E-02 4.50E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-14: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Biomass

No. of sources = 42 42

No. in MACT floor = 6 6

Avge of top 12% = 2.72E-07 -1.52E+01

Std Deviation of top 12% = 1.33E-07 5.09E-01

Skewness = 0.89 -0.34

Kurtosis = 0.28 0.10

SE Skewness 0.52 0.52

Skewness Test normal normal

SE Kurtosis 1.04 1.04

Kurtosis Test normal normal

Number of test runs = 22 22

Number of test runs that contained non-detect 

values

11 11

Highest test run = 5.56E-07 -1.44E+01

99% t-statistic for UPL 2.52E+00 2.52E+00

99% UPL of top 12% (test runs) = 4.79E-07 5.33E-07

Coal

No. of sources = 265 265

No. in MACT floor = 32 32

Avge of top 12% = 5.54E-07 -1.50E+01

Std Deviation of top 12% = 7.30E-07 1.20E+00

Skewness = 3.90 -0.61

Kurtosis = 18.60 0.46

SE Skewness 0.21 0.21

Skewness Test non-normal normal

SE Kurtosis 0.43 0.43

Kurtosis Test non-normal normal

Number of test runs = 132 132

Number of test runs that contained non-detect 

values

42 42

Highest test run = 5.07E-06 -1.22E+01

99% t-statistic for UPL 2.36E+00 2.36E+00

99% UPL of top 12% (test runs) = 1.56E-06 1.59E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-14: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Liquid

No. of sources = 173 173

No. in MACT floor = 21 21

Avge of top 12% = 1.72E-06 -1.36E+01

Std Deviation of top 12% = 8.01E-07 1.08E+00

Skewness = -1.34 -1.74

Kurtosis = -0.12 1.59

SE Skewness 0.18 0.18

Skewness Test normal normal

SE Kurtosis 0.36 0.36

Kurtosis Test normal non-normal

Number of test runs = 188 188

Number of test runs that contained non-detect 

values

168 168

Highest test run = 2.25E-06 -1.30E+01

99% t-statistic for UPL 2.35E+00 2.35E+00

99% UPL of top 12% (test runs) = 2.81E-06 5.45E-06

Gas 1

No. of sources = 13 13

No. in MACT floor = 2 2

Avge of top 12% = 1.07E-07 -1.61E+01

Std Deviation of top 12% = 3.73E-08 3.49E-01

Skewness = 0.64 -0.01

Kurtosis = -0.27 -0.12

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.65E-07 -1.56E+01

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.96E-07 2.34E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-14: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Gas 1 - Metallurgical Furnaces

No. of sources = 7 7

No. in MACT floor = 1 1

Avge of top 12% = 3.32E-08 -1.74E+01

Std Deviation of top 12% = 2.65E-08 8.31E-01

Skewness = 1.29 0.38

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 6.28E-08 -1.66E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.84E-07 2.98E-06

Gas 2

No. of sources = 8 8

No. in MACT floor = 1 1

Avge of top 12% = 8.25E-08 -1.63E+01

Std Deviation of top 12% = 1.82E-08 2.13E-01

Skewness = 1.38 1.24

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.03E-07 -1.61E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.86E-07 2.73E-07

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-15: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Biomass

No. of sources = 51 51

No. in MACT floor = 7 7

Avge of top 12% = 6.09E-03 -7.45E+00

Std Deviation of top 12% = 1.41E-02 2.44E+00

Skewness = 2.93 -0.07

Kurtosis = 8.63 0.07

SE Skewness 0.39 0.39

Skewness Test non-normal normal

SE Kurtosis 0.78 0.78

Kurtosis Test non-normal normal

Number of test runs = 39 39

Number of test runs that contained non-detect 

values

4 4

Highest test run = 6.43E-02 -2.74E+00

99% t-statistic for UPL 2.43E+00 2.43E+00

99% UPL of top 12% (test runs) = 2.67E-02 2.02E-02

Coal

No. of sources = 296 296

No. in MACT floor = 36 36

Avge of top 12% = 4.70E-03 -7.04E+00

Std Deviation of top 12% = 2.03E-02 1.62E+00

Skewness = 6.48 0.06

Kurtosis = 41.01 1.35

SE Skewness 0.21 0.21

Skewness Test non-normal normal

SE Kurtosis 0.42 0.42

Kurtosis Test non-normal non-normal

Number of test runs = 136 136

Number of test runs that contained non-detect 

values

21 21

Highest test run = 1.40E-01 -1.97E+00

99% t-statistic for UPL 2.35E+00 2.35E+00

99% UPL of top 12% (test runs) = 3.26E-02 8.05E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-15: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Liquid

No. of sources = 185 185

No. in MACT floor = 23 23

Avge of top 12% = 2.67E-04 -8.28E+00

Std Deviation of top 12% = 6.27E-05 5.70E-01

Skewness = 3.55 -9.89

Kurtosis = 25.01 107.51

SE Skewness 0.22 0.22

Skewness Test non-normal normal

SE Kurtosis 0.43 0.43

Kurtosis Test non-normal non-normal

Number of test runs = 127 127

Number of test runs that contained non-detect 

values

118 118

Highest test run = 6.24E-04 -7.38E+00

99% t-statistic for UPL 2.36E+00 2.36E+00

99% UPL of top 12% (test runs) = 3.54E-04 5.54E-04

Gas 1

No. of sources = 10 10

No. in MACT floor = 2 2

Avge of top 12% = 1.01E-04 -9.29E+00

Std Deviation of top 12% = 3.91E-05 5.02E-01

Skewness = -1.08 -1.39

Kurtosis = -0.72 0.79

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

5 5

Highest test run = 1.30E-04 -8.95E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.94E-04 3.04E-04

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-15: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Gas 1 - metallurgical furnaces

No. of sources = 0 0

No. in MACT floor = 5 5

Avge of top 12% = 1.66E-04 -8.84E+00

Std Deviation of top 12% = 8.80E-05 5.84E-01

Skewness = 0.00 -0.07

Kurtosis = -3.20 -3.09

SE Skewness 1.00 1.00

Skewness Test normal normal

SE Kurtosis 2.00 2.00

Kurtosis Test normal normal

Number of test runs = 6 6

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.54E-04 -8.28E+00

99% t-statistic for UPL 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 3.75E-04 5.82E-04

Gas 2

No. of sources = 8 8

No. in MACT floor = 1 1

Avge of top 12% = 1.70E-06 -1.33E+01

Std Deviation of top 12% = 1.41E-07 8.25E-02

Skewness = 0.63 0.51

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.85E-06 -1.32E+01

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 2.50E-06 2.71E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-16: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Liquid

No. of sources = 106 106

No. in MACT floor = 13 13

Avge of top 12% = 4.09E-01 -1.24E+00

Std Deviation of top 12% = 3.06E-01 9.21E-01

Skewness = 0.77 -0.52

Kurtosis = -0.25 -0.54

SE Skewness 0.40 0.40

Skewness Test normal normal

SE Kurtosis 0.81 0.81

Kurtosis Test normal normal

Number of test runs = 37 37

Number of test runs that contained non-detect 

values

11 11

Highest test run = 1.22E+00 1.95E-01

99% t-statistic for UPL 2.43E+00 2.43E+00

99% UPL of top 12% (test runs) = 8.56E-01 1.12E+00

Gas 1

No. of sources = 753 753

No. in MACT floor = 91 91

Avge of top 12% = 1.46E+00 -1.96E+00

Std Deviation of top 12% = 1.17E+01 1.32E+00

Skewness = 13.65 2.12

Kurtosis = 204.57 7.06

SE Skewness 0.14 0.14

Skewness Test non-normal non-normal

SE Kurtosis 0.29 0.29

Kurtosis Test non-normal non-normal

Number of test runs = 295 295

Number of test runs that contained non-detect 

values

120 120

Highest test run = 1.84E+02 5.21E+00

99% t-statistic for UPL 2.34E+00 2.34E+00

99% UPL of top 12% (test runs) = 1.73E+01 8.45E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-16: UPL Calculations for Existing Units under Alternative Solid Waste Definition

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Gas 1 - metallurgical furnaces

No. of sources = 16 16

No. in MACT floor = 0 0

Avge of top 12% = 8.67E-01 -3.65E-01

Std Deviation of top 12% = 5.00E-01 8.20E-01

Skewness = -0.25 -1.23

Kurtosis = -1.84 1.19

SE Skewness 0.93 0.93

Skewness Test normal normal

SE Kurtosis 1.85 1.85

Kurtosis Test normal normal

Number of test runs = 7 7

Number of test runs that contained non-detect 

values

3 3

Highest test run = 1.35E+00 3.03E-01

99% t-statistic for UPL 3.14E+00 3.14E+00

99% UPL of top 12% (test runs) = 1.95E+00 4.11E+00

Gas 2

No. of sources = 74 74

No. in MACT floor = 9 9

Avge of top 12% = 9.12E-02 -2.49E+00

Std Deviation of top 12% = 2.83E-02 5.27E-01

Skewness = -2.05 -2.23

Kurtosis = 2.70 3.49

SE Skewness 0.47 0.47

Skewness Test normal normal

SE Kurtosis 0.94 0.94

Kurtosis Test non-normal non-normal

Number of test runs = 27 27

Number of test runs that contained non-detect 

values

23 23

Highest test run = 1.10E-01 -2.21E+00

99% t-statistic for UPL 2.48E+00 2.48E+00

99% UPL of top 12% (test runs) = 1.34E-01 1.84E-01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-16: UPL Calculations for Existing Units under Alternative Solid Waste Definition

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Dutch Oven

No. of sources = 13 13

No. in MACT floor = 2 2

Avge of top 12% = 3.82E+02 5.60E+00

Std Deviation of top 12% = 3.34E+02 9.42E-01

Skewness = 2.33 -1.16

Kurtosis = 6.70 2.78

SE Skewness 0.37 0.37

Skewness Test non-normal normal

SE Kurtosis 0.73 0.73

Kurtosis Test non-normal non-normal

Number of test runs = 45 45

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.72E+03 7.45E+00

99% t-statistic for UPL 2.41E+00 2.41E+00

99% UPL of top 12% (test runs) = 8.63E+02 1.05E+03

Biomass - Fluidized Bed

No. of sources = 1 1

No. in MACT floor = 1 1

Avge of top 12% = 3,552 8.14E+00

Std Deviation of top 12% = 1,248 3.31E-01

Skewness = 1.59 1.47

Kurtosis = #DIV/0! #DIV/0!

SE Skewness 1.41 1.41

Skewness Test normal normal

SE Kurtosis 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0!

Number of test runs = 3 3

Number of test runs that contained non-detect 

values

0 0

Highest test run = 4.98E+03 8.51E+00

99% t-statistic for UPL 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.06E+04 2.25E+04

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-16: UPL Calculations for Existing Units under Alternative Solid Waste Definition

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Fuel Cell

No. of sources = 11 11

No. in MACT floor = 5 5

Avge of top 12% = 2.02E+02 5.04E+00

Std Deviation of top 12% = 1.50E+02 7.55E-01

Skewness = 1.17 -0.01

Kurtosis = 0.57 -0.94

SE Skewness 0.34 0.34

Skewness Test non-normal normal

SE Kurtosis 0.67 0.67

Kurtosis Test normal normal

Number of test runs = 53 53

Number of test runs that contained non-detect 

values

0 0

Highest test run = 5.74E+02 6.35E+00

99% t-statistic for UPL 2.40E+00 2.40E+00

99% UPL of top 12% (test runs) = 4.16E+02 4.54E+02

Biomass - Stoker

No. of sources = 71 71

No. in MACT floor = 9 9

Avge of top 12% = 1.03E+02 4.54E+00

Std Deviation of top 12% = 4.73E+01 4.30E-01

Skewness = 1.35 0.19

Kurtosis = 2.01 -0.20

SE Skewness 0.39 0.39

Skewness Test non-normal normal

SE Kurtosis 0.78 0.78

Kurtosis Test non-normal normal

Number of test runs = 39 39

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.36E+02 5.47E+00

99% t-statistic for UPL 2.43E+00 2.43E+00

99% UPL of top 12% (test runs) = 1.72E+02 1.76E+02

Coal - FB

No. of sources = 12 12

No. in MACT floor = 5 5

Avge of top 12% = 2.46E+01 3.11E+00

Std Deviation of top 12% = 8.26E+00 5.16E-01

Skewness = -0.68 -2.52

Kurtosis = 0.85 7.81

SE Skewness 0.47 0.47

Skewness Test normal normal

SE Kurtosis 0.94 0.94

Kurtosis Test normal non-normal

Number of test runs = 27 27

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.98E+01 3.68E+00

99% t-statistic for UPL 2.48E+00 2.48E+00

99% UPL of top 12% (test runs) = 3.71E+01 4.89E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-16: UPL Calculations for Existing Units under Alternative Solid Waste Definition

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Coal - PC

No. of sources = 39 39

No. in MACT floor = 5 5

Avge of top 12% = 1.92E+01 -2.38E-01

Std Deviation of top 12% = 3.29E+01 3.04E+00

Skewness = 1.24 0.59

Kurtosis = -0.50 -1.34

SE Skewness 0.50 0.50

Skewness Test non-normal normal

SE Kurtosis 1.00 1.00

Kurtosis Test normal normal

Number of test runs = 24 24

Number of test runs that contained non-detect 

values

0 0

Highest test run = 7.79E+01 4.36E+00

99% t-statistic for UPL 2.50E+00 2.50E+00

99% UPL of top 12% (test runs) = 6.97E+01 8.28E+01

Coal - Stoker

No. of sources = 45 45

No. in MACT floor = 6 6

Avge of top 12% = 1.75E+01 2.72E+00

Std Deviation of top 12% = 7.87E+00 6.27E-01

Skewness = -0.13 -1.38

Kurtosis = 0.34 1.04

SE Skewness 0.58 0.58

Skewness Test normal normal

SE Kurtosis 1.15 1.15

Kurtosis Test normal normal

Number of test runs = 18 18

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.41E+01 3.53E+00

99% t-statistic for UPL 2.57E+00 2.57E+00

99% UPL of top 12% (test runs) = 3.01E+01 4.15E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-17: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values) Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Liquid

No. of sources = 14 14 14 14

No. in MACT floor = 2 2 2 2

Avge of top 12% = 5.32E-03 -5.54E+00 1.10E-03 -6.83E+00

Std Deviation of top 12% = 3.95E-03 9.05E-01 1.77E-04 1.75E-01

Skewness = 0.09 -0.09 -1.10 -1.38

Kurtosis = -2.98 -2.91 1.14 2.01

SE Skewness 1.00 1.00 1.00 1.00

Skewness Test normal normal normal normal

SE Kurtosis 2.00 2.00 2.00 2.00

Kurtosis Test normal normal normal normal

Number of test runs = 6 6 6 6

Number of test runs that contained non-detect 

values

33 6 6

Highest test run = 9.90E-03 -4.62E+00 1.28E-03 -6.66E+00

99% t-statistic for UPL 3.36E+00 3.36E+00 3.36E+00 3.36E+00

99% UPL of top 12% (test runs) = 1.47E-02 3.37E-02 1.52E-03 1.65E-03

Gas 1

No. of sources = 7 7 7 7

No. in MACT floor = 1 1 1 1

Avge of top 12% = 1.26E-01 -2.07E+00 2.57E-03 -6.06E+00

Std Deviation of top 12% = 1.18E-02 9.33E-02 1.23E-03 5.52E-01

Skewness = 0.14 0.00 -0.47 -1.08

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

33 2 2

Highest test run = 1.38E-01 -1.98E+00 3.73E-03 -5.59E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.93E-01 2.14E-01 9.59E-03 5.41E-02

Total MASS TEQ

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-17: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values) Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Total MASS TEQ

Gas 1 - Metallurgical Furnaces

No. of sources = 7 7 7 7

No. in MACT floor = 1 1 1 1

Avge of top 12% = 1.27E-02 -4.37E+00 2.58E-03 -5.96E+00

Std Deviation of top 12% = 2.12E-18 0.00E+00 2.15E-04 8.58E-02

Skewness = -2.45 #DIV/0! -1.73 -1.73

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal #DIV/0! normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

33 3 3

Highest test run = 1.27E-02 -4.37E+00 2.70E-03 -5.91E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.27E-02 1.27E-02 3.80E-03 4.19E-03

Gas 2

No. of sources = 5 5 5 5

No. in MACT floor = 1 1 1 1

Avge of top 12% = 4.50E-02 -3.18E+00 2.67E-03 -5.97E+00

Std Deviation of top 12% = 2.03E-02 5.02E-01 9.86E-04 3.46E-01

Skewness = -0.30 -0.92 1.64 1.56

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

33 3 3

Highest test run = 6.46E-02 -2.74E+00 3.80E-03 -5.57E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.60E-01 7.23E-01 8.28E-03 1.83E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-17: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values) Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Total MASS TEQ

MACT Floor by Combustor Reported Values LN(reported values) Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Dutch Oven

No. of sources = 2 2 2 2

No. in MACT floor = 1 1 1 1

Avge of top 12% = 9.12E+00 2.16E+00 9.53E-02 -2.39E+00

Std Deviation of top 12% = 3.74E+00 3.85E-01 3.39E-02 3.35E-01

Skewness = 1.59 1.46 1.60 1.50

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

33 3 3

Highest test run = 1.34E+01 2.60E+00 1.34E-01 -2.01E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 3.04E+01 7.73E+01 2.88E-01 6.14E-01

Biomass - Fluidized Bed

No. of sources = 1 1 1 1

No. in MACT floor = 1 1 1 1

Avge of top 12% = 1.83E-01 -2.45E+00 1.09E-02 -5.18E+00

Std Deviation of top 12% = 2.54E-01 1.48E+00 1.44E-02 1.37E+00

Skewness = 1.73 1.73 1.73 1.73

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

33 3 3

Highest test run = 4.76E-01 -7.42E-01 2.74E-02 -3.60E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 1.63E+00 3.91E+02 9.25E-02 1.36E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-17: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values) Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Total MASS TEQ

Biomass - Fuel Cell

No. of sources = 5 5 5 5

No. in MACT floor = 5 5 5 5

Avge of top 12% = 2.04E-01 -2.63E+00 5.52E-03 -6.21E+00

Std Deviation of top 12% = 2.46E-01 2.01E+00 5.43E-03 1.99E+00

Skewness = 1.66 -1.42 0.75 -0.98

Kurtosis = 2.78 2.94 -0.86 -0.11

SE Skewness 0.68 0.68 0.68 0.68

Skewness Test non-normal normal normal normal

SE Kurtosis 1.36 1.36 1.36 1.36

Kurtosis Test non-normal non-normal normal normal

Number of test runs = 13 13 13 13

Number of test runs that contained non-detect 

values

11 11 13 13

Highest test run = 8.40E-01 -1.75E-01 1.48E-02 -4.21E+00

99% t-statistic for UPL 2.68E+00 2.68E+00 2.68E+00 2.68E+00

99% UPL of top 12% (test runs) = 6.26E-01 2.30E+00 1.48E-02 6.15E-02

Biomass - Stoker

No. of sources = 3 3 3 3

No. in MACT floor = 1 1 1 1

Avge of top 12% = 5.84E-02 -2.96E+00 1.52E-05 -1.11E+01

Std Deviation of top 12% = 3.19E-02 6.12E-01 5.87E-06 3.59E-01

Skewness = 0.12 -0.72 1.72 1.71

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

22 3 3

Highest test run = 9.07E-02 -2.40E+00 2.20E-05 -1.07E+01

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 2.40E-01 1.69E+00 4.86E-05 1.12E-04

Coal - FB

No. of sources = 8 8 8 8

No. in MACT floor = 5 5 5 5

Avge of top 12% = 7.23E-02 -3.48E+00 3.22E-03 -6.03E+00

Std Deviation of top 12% = 6.01E-02 1.79E+00 2.44E-03 8.17E-01

Skewness = 0.23 -0.84 0.86 0.03

Kurtosis = -0.92 -1.13 -0.48 -1.52

SE Skewness 0.63 0.63 0.63 0.63

Skewness Test normal normal normal normal

SE Kurtosis 1.26 1.26 1.26 1.26

Kurtosis Test normal normal normal normal

Number of test runs = 15 15 15 15

Number of test runs that contained non-detect 

values

6 6 15 15

Highest test run = 1.91E-01 -1.66E+00 7.72E-03 -4.86E+00

99% t-statistic for UPL 2.62E+00 2.62E+00 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 1.72E-01 6.02E-01 7.27E-03 9.32E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix G-17: UPL Calculations for Existing Units under Alternative Solid Waste Definition

MACT Floor by Fuel Type Reported Values LN(reported values) Reported Values LN(reported values)

Parameters

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

PCDD/PCDF

(ng/dscm @ 7% O2)

Total MASS TEQ

Coal - PC

No. of sources = 8 8 8 8

No. in MACT floor = 1 1 1 1

Avge of top 12% = 1.82E-02 -4.04E+00 2.12E-03 -6.16E+00

Std Deviation of top 12% = 6.13E-03 3.16E-01 2.94E-04 1.37E-01

Skewness = 1.66 1.61 0.78 0.60

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

33 3 3

Highest test run = 2.52E-02 -3.68E+00 2.44E-03 -6.02E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 5.30E-02 1.06E-01 3.80E-03 4.60E-03

Coal - Stoker 42 44

No. of sources = 8 8 8 8

No. in MACT floor = 1 1 1 1

Avge of top 12% = 2.53E-03 -6.00E+00 1.52E-03 -6.50E+00

Std Deviation of top 12% = 5.86E-04 2.22E-01 2.30E-04 1.46E-01

Skewness = 1.51 1.41 1.56 1.51

Kurtosis = #DIV/0! #DIV/0! #DIV/0! #DIV/0!

SE Skewness 1.41 1.41 1.41 1.41

Skewness Test normal normal normal normal

SE Kurtosis 2.83 2.83 2.83 2.83

Kurtosis Test #DIV/0! #DIV/0! #DIV/0! #DIV/0!

Number of test runs = 3 3 3 3

Number of test runs that contained non-detect 

values

00 3 3

Highest test run = 3.20E-03 -5.74E+00 1.78E-03 -6.33E+00

99% t-statistic for UPL 6.96E+00 6.96E+00 6.96E+00 6.96E+00

99% UPL of top 12% (test runs) = 5.87E-03 8.79E-03 2.82E-03 3.46E-03

Yellow highlight indicates the distribution (either normal or lognormal)
MACT Floor by Fuel Type

Parameters

PM 

Filterable

(lb/mmBtu) Hg HCl CO

D/F 

total mass

D/F

TEQ

Total Count of 

Units in 

Subcategory

Biomass 420

No. of sources = 192 91 92

No. in MACT floor = 24 11 12 0

Coal 578

No. of sources = 366 285 318

No. in MACT floor = 44 35 39 0

Liquid 826

No. of sources = 91 177 190 116 17 17

No. in MACT floor = 11 22 23 14 5 5

Gas 1 - Excluding Metal Industry Furnaces 10783

No. of sources = 144 14 11 754 8 8

No. in MACT floor = 18 5 5 91 5 5

Gas 1 - Metal Industry Furnaces 749

No. of sources = 9 7 9 15 7 7

No. in MACT floor = 5 5 5 5 5 5

Gas 2 199

No. of sources = 13 8 8 75 5 5

No. in MACT floor = 5 5 5 9 5 5

Parameters

CO (ppm @ 

3% O2)

Dioxin/Fura

ns (Total 

Mass)

ppm@ 3% 

O2)

Dioxin/Fura

ns (TEQ)

ppm@ 3% 

O2)

Total Count of 

Units in 

Subcategory

Biomass - Dutch Oven 62

No. of sources = 17 3 3

No. in MACT floor = 5 3 3

Biomass - Fluidized Bed 12

No. of sources = 7 6 6

No. in MACT floor = 5 5 5

Biomass - Fuel Cell 26

No. of sources = 16 7 7

No. in MACT floor = 5 5 5

Biomass - Stoker 320

No. of sources = 119 16 16

No. in MACT floor = 15 5 5

Coal - FB 31

No. of sources = 17 12 12

No. in MACT floor = 5 5 5

Coal - PC 186

No. of sources = 41 10 10

No. in MACT floor = 5 5 5

Coal - Stoker 361

No. of sources = 61 14 14

No. in MACT floor = 8 5 5

Represents subcategories where less than five sources were used for the proposed MACT floor emission limits.

Appendix H-1: Summary of Number of Sources with Test Data and Top 12 Percent 

Using Data From a Minimum of Five Sources
Appendix H-2: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Gas 1 - Metal Industry Furnaces

No. of sources = 15 15

No. in MACT floor = 5 5

Avge of top 12% = 8.03E+00 7.14E-01

Std Deviation of top 12% = 1.00E+01 2.02E+00

Skewness = 0.91 -0.04

Kurtosis = -0.70 -1.52

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

3 3

Highest test run = 2.84E+01 3.35E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 2.47E+01 5.85E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-2: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

CO

(ppm @ 3% O2)

CO

(ppm @ 3% O2)

Biomass - Dutch Oven

No. of sources = 17 17

No. in MACT floor = 5 5

Avge of top 12% = 7.99E+02 6.10E+00

Std Deviation of top 12% = 7.83E+02 1.28E+00

Skewness = 1.33 -0.95

Kurtosis = 1.04 1.18

SE Skewness 0.26 0.26

Skewness Test non-normal normal

SE Kurtosis 0.53 0.53

Kurtosis Test normal non-normal

Number of test runs = 87 87

Number of test runs that contained non-detect 

values

0 0

Highest test run = 3.15E+03 8.06E+00

99% t-statistic for UPL 2.37E+00 2.37E+00

99% UPL of top 12% (test runs) = 1.89E+03 2.65E+03

Coal - FB

No. of sources = 17 17

No. in MACT floor = 5 5

Avge of top 12% = 1.80E+01 2.81E+00

Std Deviation of top 12% = 6.08E+00 4.90E-01

Skewness = -0.81 -2.18

Kurtosis = 0.30 5.74

SE Skewness 0.53 0.53

Skewness Test normal normal

SE Kurtosis 1.07 1.07

Kurtosis Test normal non-normal

Number of test runs = 21 21

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.52E+01 3.23E+00

99% t-statistic for UPL 2.53E+00 2.53E+00

99% UPL of top 12% (test runs) = 2.75E+01 3.56E+01

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-3: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

PM Filterable

(lb/mmBtu)

PM Filterable

(lb/mmBtu)

Gas 1 - Metal Industry Furnaces

No. of sources = 9 9

No. in MACT floor = 5 5

Avge of top 12% = 3.42E-03 -6.86E+00

Std Deviation of top 12% = 4.35E-03 2.41E+00

Skewness = 1.98 -1.65

Kurtosis = 3.09 1.94

SE Skewness 0.53 0.53

Skewness Test non-normal normal

SE Kurtosis 1.07 1.07

Kurtosis Test non-normal normal

Number of test runs = 21 21

Number of test runs that contained non-detect 

values

0 0

Highest test run = 1.53E-02 -4.18E+00

99% t-statistic for UPL 2.53E+00 2.53E+00

99% UPL of top 12% (test runs) = 1.02E-02 4.49E-02

Gas 2

No. of sources = 13 13

No. in MACT floor = 5 5

Avge of top 12% = 8.85E-03 -5.47E+00

Std Deviation of top 12% = 1.05E-02 1.34E+00

Skewness = 1.65 -0.21

Kurtosis = 2.09 -0.58

SE Skewness 0.37 0.37

Skewness Test non-normal normal

SE Kurtosis 0.73 0.73

Kurtosis Test non-normal normal

Number of test runs = 45 45

Number of test runs that contained non-detect 

values

1 1

Highest test run = 4.21E-02 -3.17E+00

99% t-statistic for UPL 2.41E+00 2.41E+00

99% UPL of top 12% (test runs) = 2.39E-02 2.91E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-4: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 14 14

No. in MACT floor = 5 5

Avge of top 12% = 1.60E-07 -1.57E+01

Std Deviation of top 12% = 6.45E-08 4.48E-01

Skewness = -0.04 -0.44

Kurtosis = -1.77 -1.07

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

0 0

Highest test run = 2.30E-07 -1.53E+01

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 2.67E-07 3.09E-07

Gas 1 - Metal Industry Furnaces

No. of sources = 7 7

No. in MACT floor = 5 5

Avge of top 12% = 4.46E-07 -1.54E+01

Std Deviation of top 12% = 4.64E-07 1.45E+00

Skewness = 0.84 -0.41

Kurtosis = -0.80 -0.66

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

6 6

Highest test run = 1.32E-06 -1.35E+01

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 1.22E-06 2.34E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-4: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

Hg

(lb/mmBtu)

Hg

(lb/mmBtu)

Gas 2

No. of sources = 8 8

No. in MACT floor = 5 5

Avge of top 12% = 2.91E-07 -1.59E+01

Std Deviation of top 12% = 2.80E-07 2.44E+00

Skewness = 2.38 -2.63

Kurtosis = 8.18 6.59

SE Skewness 0.51 0.51

Skewness Test non-normal normal

SE Kurtosis 1.02 1.02

Kurtosis Test non-normal non-normal

Number of test runs = 23 23

Number of test runs that contained non-detect 

values

17 17

Highest test run = 1.33E-06 -1.35E+01

99% t-statistic for UPL 2.51E+00 2.51E+00

99% UPL of top 12% (test runs) = 7.22E-07 5.06E-06

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-5: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 11 11

No. in MACT floor = 5 5

Avge of top 12% = 1.34E-04 -8.99E+00

Std Deviation of top 12% = 4.92E-05 4.35E-01

Skewness = 0.48 -1.39

Kurtosis = 1.90 3.50

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal non-normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

8 8

Highest test run = 2.48E-04 -8.30E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 2.16E-04 2.56E-04

Gas 1 - Metal Industry Furnaces

No. of sources = 9 9

No. in MACT floor = 5 5

Avge of top 12% = 2.64E-04 -8.38E+00

Std Deviation of top 12% = 1.28E-04 5.88E-01

Skewness = 0.13 -0.80

Kurtosis = -0.79 -0.29

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

6 6

Highest test run = 4.90E-04 -7.62E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 4.76E-04 6.10E-04

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-5: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

HCl

(lb/mmBtu)

HCl

(lb/mmBtu)

Gas 2

No. of sources = 8 8

No. in MACT floor = 5 5

Avge of top 12% = 1.63E-03 -7.76E+00

Std Deviation of top 12% = 1.98E-03 2.43E+00

Skewness = 1.09 -1.37

Kurtosis = -0.49 1.46

SE Skewness 0.50 0.50

Skewness Test non-normal normal

SE Kurtosis 1.00 1.00

Kurtosis Test normal normal

Number of test runs = 24 24

Number of test runs that contained non-detect 

values

3 3

Highest test run = 5.60E-03 -5.18E+00

99% t-statistic for UPL 2.50E+00 2.50E+00

99% UPL of top 12% (test runs) = 4.66E-03 1.76E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-6: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Fuel Type Reported Values LN(reported values)

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Liquid 47 61

No. of sources = 17 17

No. in MACT floor = 5 5

Avge of top 12% = 1.40E-03 -7.69E+00

Std Deviation of top 12% = 9.86E-04 2.63E+00

Skewness = 0.08 -1.58

Kurtosis = -0.80 0.75

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 3.17E-03 -5.75E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 3.04E-03 3.60E-02

Gas 1 - Excluding Metal Industry Furnaces

No. of sources = 8 8

No. in MACT floor = 5 5

Avge of top 12% = 4.10E-03 -5.56E+00

Std Deviation of top 12% = 1.35E-03 3.82E-01

Skewness = 0.78 -1.56

Kurtosis = 4.30 5.43

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test non-normal non-normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 7.75E-03 -4.86E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 6.35E-03 7.29E-03

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-6: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

Gas 1 - Metal Industry Furnaces

No. of sources = 7 7

No. in MACT floor = 5 5

Avge of top 12% = 8.21E-03 -5.09E+00

Std Deviation of top 12% = 6.53E-03 7.91E-01

Skewness = 1.01 0.33

Kurtosis = -0.29 -1.49

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 2.16E-02 -3.83E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 1.90E-02 2.28E-02

Gas 2

No. of sources = 5 5

No. in MACT floor = 5 5

Avge of top 12% = 8.82E-03 -5.26E+00

Std Deviation of top 12% = 1.01E-02 1.08E+00

Skewness = 2.15 0.17

Kurtosis = 5.38 -0.68

SE Skewness 0.63 0.63

Skewness Test non-normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test non-normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 3.91E-02 -3.24E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 2.56E-02 3.12E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-6: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

MACT Floor by Combustor Reported Values LN(reported values)

Parameters

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

TEQ PCDD/PCDF

(ng/dscm @ 7% O2)

Biomass - Dutch Oven

No. of sources = 3 3

No. in MACT floor = 3 3

Avge of top 12% = 1.57E-01 -2.70E+00

Std Deviation of top 12% = 1.67E-01 1.63E+00

Skewness = 0.82 -0.37

Kurtosis = -1.09 -1.57

SE Skewness 0.82 0.82

Skewness Test normal normal

SE Kurtosis 1.63 1.63

Kurtosis Test normal normal

Number of test runs = 9 9

Number of test runs that contained non-detect 

values

9 9

Highest test run = 4.22E-01 -8.62E-01

99% t-statistic for UPL 2.90E+00 2.90E+00

99% UPL of top 12% (test runs) = 4.80E-01 1.57E+00

Biomass - Fluidized Bed

No. of sources = 6 6

No. in MACT floor = 5 5

Avge of top 12% = 6.23E-03 -5.45E+00

Std Deviation of top 12% = 7.23E-03 7.92E-01

Skewness = 2.43 1.31

Kurtosis = 5.50 1.38

SE Skewness 0.63 0.63

Skewness Test non-normal non-normal

SE Kurtosis 1.26 1.26

Kurtosis Test non-normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 2.74E-02 -3.60E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 1.82E-02 1.59E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-6: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

Biomass - Stoker

No. of sources = 16 16

No. in MACT floor = 5 5

Avge of top 12% = 1.56E-03 -7.48E+00

Std Deviation of top 12% = 1.18E-03 2.24E+00

Skewness = -0.10 -1.23

Kurtosis = -1.49 -0.36

SE Skewness 0.71 0.71

Skewness Test normal normal

SE Kurtosis 1.41 1.41

Kurtosis Test normal normal

Number of test runs = 12 12

Number of test runs that contained non-detect 

values

10 10

Highest test run = 3.21E-03 -5.74E+00

99% t-statistic for UPL 2.72E+00 2.72E+00

99% UPL of top 12% (test runs) = 3.62E-03 2.89E-02

Coal - FB

No. of sources = 12 12

No. in MACT floor = 5 5

Avge of top 12% = 1.75E-03 -7.38E+00

Std Deviation of top 12% = 1.46E-03 2.29E+00

Skewness = 0.41 -1.43

Kurtosis = -1.41 0.54

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

9 9

Highest test run = 4.01E-03 -5.52E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 4.18E-03 2.78E-02

Yellow highlight indicates the distribution (either normal or lognormal)
Appendix H-6: UPL Calculations for Existing Units Using a Minimum of Five Data Sources

Coal - PC

No. of sources = 10 10

No. in MACT floor = 5 5

Avge of top 12% = 2.85E-03 -6.01E+00

Std Deviation of top 12% = 1.61E-03 5.80E-01

Skewness = 0.93 -0.12

Kurtosis = 0.39 -0.73

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

15 15

Highest test run = 6.45E-03 -5.04E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 5.52E-03 6.42E-03

Coal - Stoker

No. of sources = 14 14

No. in MACT floor = 5 5

Avge of top 12% = 2.42E-03 -6.06E+00

Std Deviation of top 12% = 6.86E-04 2.97E-01

Skewness = 0.11 -0.36

Kurtosis = -1.04 -0.66

SE Skewness 0.63 0.63

Skewness Test normal normal

SE Kurtosis 1.26 1.26

Kurtosis Test normal normal

Number of test runs = 15 15

Number of test runs that contained non-detect 

values

12 12

Highest test run = 3.46E-03 -5.67E+00

99% t-statistic for UPL 2.62E+00 2.62E+00

99% UPL of top 12% (test runs) = 3.56E-03 3.81E-03

Yellow highlight indicates the distribution (either normal or lognormal)
PM- Filterable

(lb/mmBtu)

Hg

(lb/mmBtu)

HCl

(lb/mmBtu)

CO

(ppm @3% 

O2)

CO with Load 

Variability

(ppm @3% O2)

TM D/F

(ng/dscm 

@7% O2)

TEQ D/F

(ng/dscm 

@7% O2)

COAL

Stoker/Other 4.00E-03

FB 30 5.00E-03

PC 6.00E-03

BIOMASS

Stoker/Other 4.00E-03

Fuel Cell

FB 2.00E-02

Dutch Oven 1,990 5.00E-01

LIQUID 4.00E-03

GAS 1 (NG/RFG) 

excluding Metals 

Furnaces 3.00E-07 3.00E-04 7.00E-03

GAS 1 (NG/RFG) 

including Metals 

Furnaces 5.00E-02 2.00E-06 5.00E-04 30 2.00E-02

GAS 2 (Other 

Process Gases) 3.00E-02 6.00E-06 2.00E-02 4.00E-02

Notes:

Appendix H-7: Summary of MACT Floor Emission Limits Using Data from a Minimum of Five 

Sources

If cell is blank, the data under the proposed option was already based on a minimum of five sources and no revised calculations 

were needed.

RED text indicates at least one run in MACT floor is a Non-detect value. See "Summary - Runs" worksheet for how many test runs are 

non-detect values/reported detection levels.

*For dutch oven boilers, the dioxin TEQ floor is based on three sources since no other data was available.