Name: Julie Metts

Title: Manager - Air Quality

Company: Santee Cooper

Sign Date: 6/28/2010

Name: Craig McKenzie

Title: Senior Project Manager

Company: GEL Engineering, LLC

Sign Date: 6/28/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Santee Cooper-Cross Unit #3, ICR Section 114 Testing

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 03, 2011 Page 1 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Facility Information:

Santee Cooper - Cross Generating Station U

553 Cross Station Road

Pineville SC 29468

Contact: Julie Metts, P.E.

Phone: 843-761-8000, ext. 4688

Fax: 843-761-4156

Email: jjmetts@santeecooper.com

Testing Company:

GEL Engineering, LLC

2040 Savage Road

Charleston SC 29407

Contact:Craig McKenzie

Phone: 843-769-7378

Fax: 843-769-7197

Email: cam2@gel.com

Air Permit Number:

0420-0030-B03

Permitted Source ID/Name:

Unit 3 Coal Fire Boiler

Permitted Maximum Process Rate:

5400 MMBtu/HR with steam

Max. Normal Operation Process Rate:

5400 MMBtu/HR with steam

Target Process Test Rate

5400 MMBtu/HR with stea

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Coal-Fired Boiler For Electric Generation, LNB, SCR, ESP, & FGD

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4501500030 FRS #: 4911

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stk exhaust 336 0 0 0 2790 1056 4 16

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stk exhaust Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

stk exhaust Method 25A 3 120 0

stk exhaust Hydrogen Chloride Method 26A 3 180 0

stk exhaust Hydrogen Fluoride Method 26A 3 180 0

stk exhaust Cobalt Method 29 3 240 0

Regulation Description Compound Limit Unit

NA 0

Thursday, February 03, 2011 Page 2 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

NA

stk exhaust Selenium Method 29 3 240 0

stk exhaust Nickel Method 29 3 240 0

stk exhaust Manganese Method 29 3 240 0

stk exhaust Lead Method 29 3 240 0

stk exhaust Cadmium Method 29 3 240 0

stk exhaust Arsenic Method 29 3 240 0

stk exhaust Chromium Method 29 3 240 0

stk exhaust Antimony Method 29 3 240 0

stk exhaust Beryllium Method 29 3 240 0

stk exhaust O2 Method 3A O2 3 180 0

stk exhaust Co2 Method 3A CO2 3 180 0

Organic Condensible 

Particulate

stk exhaust Method 5/OTM-28 3 240 0

stk exhaust Total Particulate Method 5/OTM-28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

stk exhaust Method 5/OTM-28 3 240 0

Thursday, February 03, 2011 Page 3 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Sampling / Stack Data Results Summary

Location stk exhaust - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stk exhaust - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 03, 2011 Page 4 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Location stk exhaust - Method 26A

Average

Run Number 1 2 3

Test Date 6/17/2010 6/17/2010 6/17/2010

Run Start Time 9:30:00 AM 1:05:00 PM 4:25:00 PM

Run Finish Time 12:21:15 PM 3:56:15 PM 7:16:15 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 108.439 110.802 110.003 109.748

Moisture Content of Stack Gas, % 15.55 12.79 15.27 14.537

Moisture Saturation at Stack Gas Temperature, % 15.03 15.03 15.03 15.030

Carbon Dioxide, % 14.48 14.37 14.37 14.407

Oxygen, % 4.92 4.91 4.85 4.893

Average Stack Gas Temperature, °F 130.00 130.00 130.00 130.000

Dry Volumetric Flow Rate, dry scfm 1,298,758.7 1,356,164.4 1,315,123.7 1,323,348.93

3

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,700,583.9 1,730,140.0 1,722,012.0 1,717,578.63

3

Percent Isokinetic of Sampling Rate, % 103.4 101.2 103.6 102.733

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location stk exhaust - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 03, 2011 Page 5 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Location stk exhaust - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 03, 2011 Page 6 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Emissions Summary

Location: stk exhaust - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 5.16E-02 4.99E-02 4.38E-02 0.048

ppm 5.56E+01 5.37E+01 4.73E+01 52.200

ppm@7%O2 4.83E+01 4.67E+01 4.10E+01 45.333

Location: stk exhaust - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 1.37E+00 1.61E-01 1.82E+00 1.117

lb/mmBtuO2 2.23E-04 2.59E-05 2.93E-04 0.000

ppm 1.53E-01 1.77E-02 2.01E-01 0.124

ppm@7%O2 1.33E-01 1.54E-02 1.74E-01 0.107

Location: stk exhaust - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.227 0.279 0.301 0.269

Elb/hr 3.60E-01 4.52E-01 4.76E-01 0.429

gr/dscf 3.23E-05 3.89E-05 4.22E-05 0.000

lb/mmBtuO2 5.90E-05 7.10E-05 7.68E-05 0.000

mg/dscm 7.39E-02 8.89E-02 9.66E-02 0.086

ppm 4.88E-02 5.87E-02 6.37E-02 0.057

ppm@7%O2 4.24E-02 5.10E-02 5.52E-02 0.050

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.34 0.222 0.22 0.261

Elb/hr 5.39E-01 3.59E-01 3.48E-01 0.415

gr/dscf 4.84E-05 3.09E-05 3.09E-05 0.000

lb/mmBtuO2 8.84E-05 5.65E-05 5.62E-05 0.000

mg/dscm 1.11E-01 7.08E-02 7.06E-02 0.084

ppm 1.33E-01 8.51E-02 8.49E-02 0.101

ppm@7%O2 1.16E-01 7.40E-02 7.35E-02 0.088

Location: stk exhaust - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00174 0.000396 0.000333 0.001

Elb/hr 2.06E-03 4.72E-04 3.96E-04 0.001

gr/dscf 1.80E-07 4.08E-08 3.44E-08 0.000

lb/mmBtuO2 3.30E-07 7.48E-08 6.29E-08 0.000

mg/dscm 4.13E-04 9.35E-05 7.88E-05 0.000

ppm 8.15E-05 1.85E-05 1.56E-05 0.000

Thursday, February 03, 2011 Page 7 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

ppm@7%O2 7.09E-05 1.61E-05 1.36E-05 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.01666 0.01159 0.01214 0.013

Elb/hr 1.98E-02 1.38E-02 1.44E-02 0.016

gr/dscf 1.73E-06 1.20E-06 1.26E-06 0.000

lb/mmBtuO2 3.16E-06 2.19E-06 2.29E-06 0.000

mg/dscm 3.95E-03 2.74E-03 2.87E-03 0.003

ppm 1.27E-03 8.78E-04 9.23E-04 0.001

ppm@7%O2 1.11E-03 7.65E-04 8.02E-04 0.001

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00005 0.00005 0.00005 0.000

Elb/hr 5.93E-05 5.96E-05 5.95E-05 0.000

gr/dscf 5.18E-09 5.16E-09 5.17E-09 0.000

lb/mmBtuO2 9.47E-09 9.44E-09 9.44E-09 0.000

mg/dscm 1.19E-05 1.18E-05 1.18E-05 0.000

ppm 3.17E-05 3.15E-05 3.16E-05 0.000

ppm@7%O2 2.76E-05 2.75E-05 2.75E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.000212 0.00027 0.000211 0.000

Elb/hr 2.52E-04 3.22E-04 2.51E-04 0.000

gr/dscf 2.20E-08 2.78E-08 2.18E-08 0.000

lb/mmBtuO2 4.02E-08 5.10E-08 3.99E-08 0.000

mg/dscm 5.03E-05 6.37E-05 4.99E-05 0.000

ppm 1.08E-05 1.36E-05 1.07E-05 0.000

ppm@7%O2 9.40E-06 1.19E-05 9.30E-06 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.03759 0.03285 0.0224 0.031

Elb/hr 4.46E-02 3.91E-02 2.67E-02 0.037

gr/dscf 3.90E-06 3.39E-06 2.32E-06 0.000

lb/mmBtuO2 7.12E-06 6.20E-06 4.23E-06 0.000

mg/dscm 8.92E-03 7.75E-03 5.30E-03 0.007

ppm 4.12E-03 3.59E-03 2.45E-03 0.003

ppm@7%O2 3.59E-03 3.13E-03 2.13E-03 0.003

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00371 0.000653 0.000724 0.002

Elb/hr 4.40E-03 7.78E-04 8.61E-04 0.002

gr/dscf 3.85E-07 6.73E-08 7.49E-08 0.000

lb/mmBtuO2 7.03E-07 1.23E-07 1.37E-07 0.000

mg/dscm 8.80E-04 1.54E-04 1.71E-04 0.000

Thursday, February 03, 2011 Page 8 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

ppm 3.59E-04 6.29E-05 6.99E-05 0.000

ppm@7%O2 3.12E-04 5.48E-05 6.08E-05 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00315 0.00169 0.0015 0.002

Elb/hr 3.74E-03 2.01E-03 1.78E-03 0.003

gr/dscf 3.26E-07 1.74E-07 1.55E-07 0.000

lb/mmBtuO2 5.97E-07 3.19E-07 2.83E-07 0.000

mg/dscm 7.47E-04 3.99E-04 3.55E-04 0.001

ppm 8.67E-05 4.63E-05 4.12E-05 0.000

ppm@7%O2 7.55E-05 4.03E-05 3.58E-05 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.01039 0.00892 0.00844 0.009

Elb/hr 1.23E-02 1.06E-02 1.00E-02 0.011

gr/dscf 1.08E-06 9.20E-07 8.73E-07 0.000

lb/mmBtuO2 1.97E-06 1.68E-06 1.59E-06 0.000

mg/dscm 2.46E-03 2.11E-03 2.00E-03 0.002

ppm 1.08E-03 9.22E-04 8.75E-04 0.001

ppm@7%O2 9.40E-04 8.03E-04 7.61E-04 0.001

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.04046 0.04101 0.02496 0.035

Elb/hr 4.80E-02 4.89E-02 2.97E-02 0.042

gr/dscf 4.19E-06 4.23E-06 2.58E-06 0.000

lb/mmBtuO2 7.67E-06 7.74E-06 4.71E-06 0.000

mg/dscm 9.60E-03 9.68E-03 5.91E-03 0.008

ppm 3.93E-03 3.96E-03 2.42E-03 0.003

ppm@7%O2 3.42E-03 3.45E-03 2.10E-03 0.003

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.1738 0.137 0.1073 0.139

Elb/hr 2.06E-01 1.63E-01 1.28E-01 0.166

gr/dscf 1.80E-05 1.41E-05 1.11E-05 0.000

lb/mmBtuO2 3.29E-05 2.59E-05 2.03E-05 0.000

mg/dscm 4.12E-02 3.23E-02 2.54E-02 0.033

ppm 1.26E-02 9.85E-03 7.74E-03 0.010

ppm@7%O2 1.10E-02 8.58E-03 6.73E-03 0.009

Location: stk exhaust - Method 5/OTM-28

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 43.3 8.1 19 23.467

Elb/hr 5.19E+01 9.73E+00 2.28E+01 28.143

Thursday, February 03, 2011 Page 9 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Process Run Data

gr/dscf 4.55E-03 8.52E-04 1.99E-03 0.002

lb/mmBtuO2 8.31E-03 1.56E-03 3.63E-03 0.005

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 31 59.6 9 33.200

Elb/hr 3.72E+01 7.16E+01 1.08E+01 39.867

gr/dscf 3.25E-03 6.27E-03 9.41E-04 0.003

lb/mmBtuO2 5.95E-03 1.15E-02 1.72E-03 0.006

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 27.7 84.9 29.2 47.267

Elb/hr 3.32E+01 1.02E+02 3.51E+01 56.767

gr/dscf 2.91E-03 8.94E-03 3.05E-03 0.005

lb/mmBtuO2 5.32E-03 1.64E-02 5.57E-03 0.009

Thursday, February 03, 2011 Page 10 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Feed Rate 444.46 kpph EPA Methods 

5/OTM28, 29; 

6/18/2010; 8:20am12:25pm

450

1 Heat Input Million Btus/million BTU using O2 5679.7 EPA Methods 

5/OTM28, 29; 

6/18/2010; 8:20am12:25pm

5400

1 Steam Output 4262 kpph EPA Methods 

5/OTM28, 29; 

6/18/2010; 8:20am12:25pm

4250

1 Gross Electric Output 647.61 MW EPA Methods 

5/OTM28, 29; 

6/18/2010; 8:20am12:25pm

625

1 Net Electric Output 606.25 MW EPA Methods 

5/OTM28, 29; 

6/18/2010; 8:20am12:25pm

590

4 Feed Rate 445.59 kpph EPA Methods 

5/OTM28, 29; 

6/18/2010; 12:45-

4:50pm

450

4 Heat Input Million Btus/million BTU using O2 5694.2 EPA Methods 

5/OTM28, 29; 

6/18/2010; 12:45-

4:50pm

5400

4 Steam Output 4283.0 kpph EPA Methods 

5/OTM28, 29; 

6/18/2010; 12:45-

4:50pm

4250

4 Gross Electric Output 644.64 MW EPA Methods 

5/OTM28, 29; 

6/18/2010; 12:45-

4:50pm

625

4 Net Electric Output 603.06 MW EPA Methods 

5/OTM28, 29; 

6/18/2010; 12:45-

4:50pm

590

5 Feed Rate 446.21 kpph EPA Methods 

5/OTM28, 29; 

6/18/2010; 

5:05pm-9:10pm

450

Thursday, February 03, 2011 Page 11 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

5 Heat Input Million Btus/million BTU using O2 5702.1 EPA Methods 

5/OTM28, 29; 

6/18/2010; 

5:05pm-9:10pm

5400

5 Steam Output 4272 kpph EPA Methods 

5/OTM28, 29; 

6/18/2010; 

5:05pm-9:10pm

4250

5 Gross Electric Output 645.64 MW EPA Methods 

5/OTM28, 29; 

6/18/2010; 

5:05pm-9:10pm

625

5 Net Electric Output 604.34 MW EPA Methods 

5/OTM28, 29; 

6/18/2010; 

5:05pm-9:10pm

590

6 Feed Rate 444.5 kpph EPA Methods 10, 

25A, 26A; 

6/17/2010; 9:30-

12:40pm

450

6 Heat Input Million Btus/million BTU using O2 5680.7 EPA Methods 10, 

25A, 26A; 

6/17/2010; 9:30-

12:40pm

5400

6 Steam Output 4266.4 kpph EPA Methods 10, 

25A, 26A; 

6/17/2010; 9:30-

12:40pm

4250

6 Gross Electric Output 647.4 MW EPA Methods 10, 

25A, 26A; 

6/17/2010; 9:30-

12:40pm

625

6 Net Electric Output 605.7 MW EPA Methods 10, 

25A, 26A; 

6/17/2010; 9:30-

12:40pm

590

7 Feed Rate 444.58 kpph EPA Methods 10, 

25A, 26A; 

6/17/2010; 

1:05pm-4:10pm

450

7 Heat Input Million Btus/million BTU using O2 5681.3 EPA Methods 10, 

25A, 26A; 

6/17/2010; 

1:05pm-4:10pm

5400

7 Steam Output 4269.5 kpph EPA Methods 10, 

25A, 26A; 

6/17/2010; 

1:05pm-4:10pm

4250

Thursday, February 03, 2011 Page 12 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

APCD Run Data

Process Lab Run Data

7 Gross Electric Output 646.6 MW EPA Methods 10, 

25A, 26A; 

6/17/2010; 

1:05pm-4:10pm

625

7 Net Electric Output 604.8 MW EPA Methods 10, 

25A, 26A; 

6/17/2010; 

1:05pm-4:10pm

590

8 Feed Rate 445.03 kpph EPA Methods 10, 

25A, 26A; 

6/17/2010; 

4:25pm-7:30pm

450

8 Heat Input Million Btus/million BTU using O2 5687.0 EPA Methods 10, 

25A, 26A; 

6/17/2010; 

4:25pm-7:30pm

5400

8 Steam Output 4260.6 kpph EPA Methods 10, 

25A, 26A; 

6/17/2010; 

4:25pm-7:30pm

4250

8 Gross Electric Output 645.76 MW EPA Methods 10, 

25A, 26A; 

6/17/2010; 

4:25pm-7:30pm

625

8 Net Electric Output 603.64 MW EPA Methods 10, 

25A, 26A; 

6/17/2010; 

4:25pm-7:30pm

590

Run Name Value UOM Comments

Target

Value

1 Electrostatic Precipitator (ESP) 0 0

1 FGD wet limestone scrubber 0 0

1 Selective catalytic Reduction (SCR) with 

ammonia injection

0 0

Thursday, February 03, 2011 Page 13 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Sampling / Stack Data Results Detail

Location stk exhaust - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 14 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Location stk exhaust - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 15 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Location stk exhaust - Method 26A

Average

Run Number 1 2 3

Test Date 6/17/2010 6/17/2010 6/17/2010

Run Start Time 9:30:00 AM 1:05:00 PM 4:25:00 PM

Run Finish Time 12:21:15 PM 3:56:15 PM 7:16:15 PM

Net Traversing Points 16 16 16

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.225 0.225 0.225 0.225

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.0161 1.0161 1.0161 1.016

Barometric Pressure, inches of Mercury 30 30 30 30.000

Average Orifice Meter Differential, inches H2O 1.21 1.28 1.25 1.247

Dry Gas Meter Volume Sampled, cubic feet 114.010 117.900 116.447 116.119

Average Dry Gas Meter Temperature, °F 107.25 114.19 111.19 110.877

Dry Gas Meter Volume Sampled, dscf 108.439 110.802 110.003 109.748

Total Moisture Liquid collected, g 424.3 345.3 421 396.867

Volume of Water Vapor, standard cubic feet 19.97 16.25 19.82 18.680

Moisture Content of Stack Gas, % 15.55 12.79 15.27 14.537

Moisture Saturation at Stack Gas Temperature, % 15.03 15.03 15.03 15.030

Dry Mole Fraction 0.8497 0.8721 0.8497 0.857

Carbon Dioxide, % 14.48 14.37 14.37 14.407

Oxygen, % 4.92 4.91 4.85 4.893

Carbon Monoxide & Nitrogen, % 80.6 80.72 80.78 80.700

Fuel Factor 1.10 1.11 1.12

Dry Molecular Weight, lb/lb-Mole 30.51 30.50 30.49 30.500

Wet Molecular weight, lb/lb-Mole 28.72 28.90 28.66 28.760

Flue Gas Static Pressure, inches of H2O 0.65 0.65 0.67 0.657

Absolute Flue Gas Pressure, inches of Mercury 30.05 30.05 30.05 30.050

Average Stack Gas Temperature, °F 130.00 130.00 130.00 130.000

Average Velocity Head, inches of H2O 0.6009945763

98709

0.626038002

098114

0.614911726

818161

0.614

Average Stack Gas Velocity, feet/second 46.03 46.83 46.61 46.490

Stack Cross-Sectional Area, square feet 615.752 615.752 615.752 615.752

Dry Volumetric Flow Rate, dry scfm 1,298,758.7 1,356,164.4 1,315,123.7 1,323,348.9

33

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,700,583.9 1,730,140.0 1,722,012.0 1,717,578.6

33

Percent Isokinetic of Sampling Rate, % 103.4 101.2 103.6 102.733

Percent Excess Air, % 30.1 29.9 29.4 29.800

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 336 336 336

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Thursday, February 03, 2011 Page 16 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Location stk exhaust - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 17 of 18
Santee Cooper-Cross Unit #3, ICR Section 114 Testing

6/28/2010

Location stk exhaust - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 18 of 18