### Name:

Title: Company: Sign Date: Name:
Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, January 31, 2011 Page 1 of 14

### Facility Information:

OUC-Stanton Energy Center
5100 South Alafaya Trail

Orlando Fl 32831

Contact: David Baez

Phone:

Fax:

Email: Testing Company:

Weston Solutions
1625 Pumphrey Ave

Auburn Al 36832

Contact: Joe Oven

Phone: 334-466-5600

Fax:

Email: Joe.Oven@WestonSolutions.com

Air Permit Number:

564 Permitted Source ID/Name: Stanton Energy Center Unit 1 1

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram:
See attached report

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width

Stack 249.84 1980 2520 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location

Carbon Monoxide Method 10 3 0 Stack Formaldehyde Method 0011 3 0 Stack Total organic compounds

(TOC) as Propane Method 25A 3 0 Stack

O2 Method 3A O2 3 0 Stack
Co2 Method 3A CO2 3 0 Stack Nitrogen oxides (NOx) Method 7E 3 0 Stack



### Monday, January 31, 2011 Page 2 of 14

### The following describes any modifications and/or deviations to the applicable test

methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
See attached report



### Monday, January 31, 2011 Page 3 of 14

### Sampling / Stack Data Results Summary



### Location Stack - Method 0011
Average

Run Number 1 2 3

Test Date 6/24/2010 6/24/2010 6/24/2010

Run Start Time 10:50:00 AM 2:54:00 PM 6:12:00 PM

Run Finish Time 1:18:00 PM 5:15:00 PM 8:34:00 PM
Net Run Time, minutes 120 120 120
Dry Gas Meter Volume Sampled, dscf 73.285 73.439 73.769 73.498
Moisture Content of Stack Gas, % 14.40 14.18 14.34 14.307
Moisture Saturation at Stack Gas Temperature, % 14.25 14.13 14.13 14.170
Carbon Dioxide, % 13 13 12.9 12.967
Oxygen, % 6.3 6.2 6.3 6.267
Average Stack Gas Temperature, °F 127.33 127.00 127.00 127.110
Dry Volumetric Flow Rate, dry scfm 1,022,396.6 1,027,826.4 1,025,025.3 1,025,082.76 7
Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,344,701.5 1,349,195.4 1,345,518.6 1,346,471.83 3
Percent Isokinetic of Sampling Rate, % 99.1 98.8 99.5 99.133
F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000



### Location Stack - Method 10
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, %
Oxygen, %
Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, %
Fuel Type

Fw

Fc



### Monday, January 31, 2011 Page 4 of 14

### Location Stack - Method 25A
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, %
Oxygen, %
Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, %
Fuel Type

Fw

Fc



### Location Stack - Method 3A CO2
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, %
Oxygen, %
Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, %
Fuel Type

Fw

Fc



### Monday, January 31, 2011 Page 5 of 14

### Location Stack - Method 3A O2
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, %
Oxygen, %
Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, %
Fuel Type

Fw

Fc



### Location Stack - Method 7E
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, %
Oxygen, %
Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, %
Fuel Type

Fw

Fc



### Monday, January 31, 2011 Page 6 of 14

### Emissions Summary

Process Run Data 

### Location: Stack - Method 0011 Compound: Formaldehyde Average
RunNumber 1 2 3 Mass_mg 0.032 0.009 0.009 0.017
Elb/hr 5.91E-02 1.67E-02 1.65E-02 0.031
lb/mmBtuO2 1.35E-05 3.76E-06 3.77E-06 0.000

ppm 1.24E-02 3.47E-03 3.45E-03 0.006 ppm@7%O2 1.18E-02 3.28E-03 3.28E-03 0.006



### Location: Stack - Method 10 Compound: Carbon Monoxide Average
Run 1 2 3
lb/mmBtuO2 8.47E-02 1.55E-01 1.18E-01 0.119

ppm 8.32E+01 1.53E+02 1.16E+02 117.400 ppm@7%O2 7.92E+01 1.45E+02 1.10E+02 111.400



### Location: Stack - Method 25A Compound: Total organic compounds (TOC) as Average
Run 1 2 3
lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000 ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000



### Location: Stack - Method 7E Compound: Nitrogen oxides (NOx) Average
Run 1 2 3
lb/mmBtuO2 2.64E-01 2.56E-01 2.56E-01 0.259

ppm 1.58E+02 1.54E+02 1.53E+02 155.000 ppm@7%O2 1.50E+02 1.46E+02 1.46E+02 147.333



### Monday, January 31, 2011 Page 7 of 14

### Process Run Data

APCD Run Data

Process Lab Run Data



### Monday, January 31, 2011 Page 8 of 14

### Sampling / Stack Data Results Detail



### Location Stack - Method 0011 Average
Run Number 1 2 3
Test Date 6/24/2010 6/24/2010 6/24/2010
Run Start Time 10:50:00 AM 2:54:00 PM 6:12:00 PM
Run Finish Time 1:18:00 PM 5:15:00 PM 8:34:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 120 120 120 Nozzle Diameter, inches 0.194 0.194 0.194 0.194
Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.986 0.986 0.986 0.986 Barometric Pressure, inches of Mercury 29.54 29.54 29.54 29.540 Average Orifice Meter Differential, inches H2O 1.40 1.41 1.40 1.403 Dry Gas Meter Volume Sampled, cubic feet 78.797 79.993 80.015 79.602 Average Dry Gas Meter Temperature, °F 94.58 101.83 99.46 98.623 Dry Gas Meter Volume Sampled, dscf 73.285 73.439 73.769 73.498 Total Moisture Liquid collected, g 261.9 257.7999999 99999 262.4 260.700

Volume of Water Vapor, standard cubic feet 12.33 12.13 12.35 12.270 Moisture Content of Stack Gas, % 14.40 14.18 14.34 14.307 Moisture Saturation at Stack Gas Temperature, % 14.25 14.13 14.13 14.170 Dry Mole Fraction 0.8575 0.8587 0.8587 0.858 Carbon Dioxide, % 13 13 12.9 12.967 Oxygen, % 6.3 6.2 6.3 6.267 Carbon Monoxide & Nitrogen, % 80.7 80.8 80.8 80.767
Fuel Factor 1.12 1.13 1.13 Dry Molecular Weight, lb/lb-Mole 30.33 30.33 30.32 30.327 Wet Molecular weight, lb/lb-Mole 28.60 28.60 28.62 28.607 Flue Gas Static Pressure, inches of H2O -0.35 -0.35 -0.35 -0.350 Absolute Flue Gas Pressure, inches of Mercury 29.51 29.51 29.51 29.510 Average Stack Gas Temperature, °F 127.33 127.00 127.00 127.110 Average Velocity Head, inches of H2O 1.2074574056 8453 1.216412831

74853 1.210700482

266 1.212

Average Stack Gas Velocity, feet/second 65.83 66.05 65.87 65.917 Stack Cross-Sectional Area, square feet 340.448 340.448 340.448 340.448 Dry Volumetric Flow Rate, dry scfm 1,022,396.6 1,027,826.4 1,025,025.3 1,025,082.7 67 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,344,701.5 1,349,195.4 1,345,518.6 1,346,471.8 33 Percent Isokinetic of Sampling Rate, % 99.1 98.8 99.5 99.133 Percent Excess Air, % 42.0 41.0 41.9 41.633 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Round Duct Diameter, inches 249.84 249.84 249.84 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0
Fw 10640 10640 10640 10,640.000
Fc 1800 1800 1800 1,800.000



### Monday, January 31, 2011 Page 9 of 14

### Location Stack - Method 10 Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, %
Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg.
Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, January 31, 2011 Page 10 of 14

### Location Stack - Method 25A Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, %
Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg.
Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, January 31, 2011 Page 11 of 14

### Location Stack - Method 3A CO2 Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, %
Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg.
Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, January 31, 2011 Page 12 of 14

### Location Stack - Method 3A O2 Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, %
Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg.
Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, January 31, 2011 Page 13 of 14

### Location Stack - Method 7E Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, %
Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg.
Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, January 31, 2011 Page 14 of 14