# Revision 4.0

1/27/09 

# Air Pollution Control Operating Permit

Minor Modification and Preconstruction Approval

Permit Activity Number: BOP090001 Program Interest Number: 07736

Mailing Address Plant Location

RICHARD R GIORDANO

PLANT MGR

COVANTA ESSEX CO

183 RAYMOND BLVD

NEWARK, NJ 07105 COVANTA ESSEX CO

183 Raymond Blvd

Newark City

Essex County

Initial Operating Permit Approval Date: July 8, 2004

Minor Modification Approval Date: September 1, 2009

Operating Permit Expiration Date: July 7, 2014

This minor modification is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C-9.2).

The equipment at the facility must be operated in accordance with the requirements of this permit.

This approval, in response to your application, merges the provisions of the previously approved operating permit

and the changes from this minor modification into a single comprehensive permit that replaces the one previously

issued. This minor modification revised Municipal Waste Combustors’ U1, OS0 compliance plan to insert PM-10

limits based on stack testing at OS Summary Ref.#41 and OS1 Ref #17 (299 TPY and 22.8 lb/hr, respectively);

revised OS Summary Ref. #16 to recognize an exemption from NSPS requirements 40 CFR 60 subpart Db; and

reduced the minimum ammonia concentration to 19% for NOx SNCRs CDs 1007-9 (U1, OS1/OS3/OS5 &

OS7/OS8/OS9 Ref.#39). The Department re-stated requirements at U1, OS Summary, Refs #98-106 to reflect new

lower limits from 40 CFR 60 Subpart Cb, effective April 28, 2009. Control device detail sheets were also revised.

Equipment at the facility referenced by this minor modification is not covered by the permit shield, pursuant to the

provisions of N.J.A.C. 7:27-22.17. Pursuant to N.J.A.C. 7:27-22.33(e), this minor modification consists of both a

preconstruction approval and operating permit approval. This operating permit does not include compliance

schedules as part of the approved compliance plan.

The permittee shall submit to the Department and to the EPA on forms provided by the Department, at the addresses

given below, a periodic compliance certification, in accordance with N.J.A.C. 7:27-22.19 and the schedule for

compliance certifications set forth in the compliance plan in this operating permit. The annual compliance

certification reporting period will cover the calendar year ending December 31. The annual compliance

certification is due to the Department and the EPA within 60 days af ter the end of each calendar year during

which this permit was in effect. Forms provided by the Department can be found on the Department's website at:

http://www.nj.gov/dep/enfor cement/compliancecertsair.htm

.

The annual compliance certification report may also be consid ered as your six month deviation report for the period

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section

F, General Provisions and Authorities



# , of this permit, if the annual compliance certification is submitted by January

30. Jon S. Corzine 

# D EPARTMENT 

# of E NVIRONMENTAL 

# P ROTECTION 

# Mark N. Mauriello

Governor Acting Commissioner

Environmental Regulation

Bureau of Operating Permits

401 E. State Street, 2 nd 

# floor, P.O. Box 27

Trenton, NJ 08625-0027

# Revision 4.0

1/27/09 New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II

Air & Environmental Quality Compliance & Enforcement Air Compliance Branch

401 East State Street, P. O. Box 422 290 Broadway

Trenton, New Jersey 08625-0422 New York, New York 10007-1866

New Jersey Department of Environmental Protection

Air and Environmental Quality Compliance & Enforcement

Metro Regional Enforcement Office

2 Babcock Place

West Orange, NJ 07052



# We are including two electronic files, PDF and RADIUS. The PDF file contains the complete operating permit for

your facility. The RADIUS file contains the Facility Name, Location, and Contact Information; the Facility Specific

Requirements (Compliance Plan) and Inventories; and any Compliance Schedules (if needed). Upon importing this

information into your personal computer with RADIUS software, you will have up-to-date information in RADIUS

format. RADIUS software, instructions, and help are available at the Department's website at

www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00 PM daily,

where you may speak to someone about any questions you may have. The Operating Permit Help Line number is

609-633-8248.

If, in your judgment, the Department is imposing any unreasonable condition of approval in this permit modification

action, you may contest the Department’s decision on the modification and request an adjudicatory hearing pursuant

to N.J.S.A. 52:14b-1 et seq. and N.J.A. C. 7:27-22.32(a). All requests for an adjudicatory hearing must be received

in writing by the Department within 20 calendar days of the date you receive this letter. The request must contain

the information requested in N.J.A.C. 7:27-1.32 and the information on the enclosed Administrative Hearing

Request Checklist and Tracking Form.

The permittee is responsible for submitting a timely and administratively complete operating permit renewal

application. The application is considered timely if it is received at least 12 months before the expiration date of the

operating permit. To be deemed administratively complete, an application for renewal of the operating permit shall

include all of the information required by the application form for the renewal and the information required pursuant

to N.J.A.C. 7:27-22.30(d). However, consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit

the renewal application at least 15 months prior to expiration of the operating permit, so that the Department can

notify the applicant of any deficiencies in the application. This will allow the permittee to correct any deficiencies,

and to better ensure that the application is administratively complete by the renewal deadline. Only applications

which are timely and administratively complete will be eligible for coverage by an application shield. The renewal

application can be found at our website, http://www.state.nj.us/dep/aqpp/downloads/forms/OPRenewal.PDF

.

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html . In addition, CAM Plans must be included as

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification

applications denied, pursuant to N.J.A.C. 7:27-22.3.

If you have any questions regarding this permit approval, please call your permit writer, Thomas Hanna, at (609)

777-0129.

Approved by:

______________________ Margaret Gardner

Air Quality Permitting Element

Enclosure

CC: Steve Riva, USEPA Region II (diskette containing modified permit)

M. Papp - NRO (w/o enclosure)

T. Hanna (w/o enclosure)

# Revision 4.0

1/27/09 

# Administrative Hearing Request **Checklist and Tracking Form**

**I. Document Being Appealed**

**Name of the Facility Program Interest** 

**(PI) Number Permit Activity** 

**Number Issuance** 

**Date**

**COVANTA ESSEX CO 07736 BOP090001**

**II. Contact Information**

**Name of Person Requesting Hearing Name of Attorney (if applicable)**

**Address: Address:** 

**Telephone: Telephone:** 

**III. Please include the following information as part of your request:**

A. The date the permittee received the permit decision,

B. **A copy of the document being appealed,**

C. The legal and factual questions you are appealing;

D. A statement as to whether or not you raised each legal and factual issues during the

permit application process;

E. Suggested revised or alternative permit conditions;

F. An estimate of the time required for the hearing;

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons;

H. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Departments processing of your hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 E. State Street, P.O. Box 402

Trenton, New Jersey 08625

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625

Phone: (609) 633-2829

**Signature Date**

# Revision 4.0

1/27/09 

# Administrative Hearing Request **Checklist and Tracking Form**

**IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the**

**permit decision, please include the following information:**

1. The date you or your agent received notice of the permit decision (include a copy of that

permit decision with your hearing request);

2. Evidence that a copy of the request has been delivered to the applicant for the permit

which is the subject of the permit decision;

3. A detailed statement of which findings of fact and/or conclusion of law you are

challenging;

4. A description of your participation in any public hearings held in connection with the

permit application and copies of any written comments you submitted;

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a

right, a reference to the applicable statute or explanation of how your property interests

are affected by the permit decision;

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the

request has been delivered to the clerks of the county and the municipality in which the

project which is the subject of the permit decision is located;

7. Suggested revised or alternative permit conditions;

8. An estimate of the time required for the hearing;

9. A request, if necessary, for a barrier-free hearing location for physically disabled persons;

10. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Department’s transmittal of the hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 East State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625

Phone: (609) 633-2829

**Signature Date**

# Revision 4.0

1/27/09 

# Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

TABLE OF CONTENTS

Section A

REASON FOR PERMIT

Section B

DEFINITIONS

Section C

POLLUTANT EMISSIONS SUMMARY

Section D

POLLUTION PREVENTION REPORTING

Section E

GENERAL PROVISIONS AND AUTHORITIES

Section F

STATE-ONLY APPLICABLE REQUIREMENTS

Section G

COMPLIANCE PLAN AND INVENTORIES

# Revision 4.0

1/27/09 

# Section A

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

REASON FOR PERMIT

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which requires the state to issue operating permits to major facilities and minor facilities that are in certain

designated source categories. This is the operating permit for the facility listed on the cover page, which includes a

minor modification revising Municipal Waste Combustors’ U1, OS0 compliance plan to insert PM-10 limits based

on stack testing at OS Summary Ref.#41 and OS1 Ref #17 (299 TPY and 22.8 lb/hr, respectively); revising OS

Summary Ref. #16 to recognize an exemption from NSPS requirements 40 CFR 60 subpart Db; and reducing the

minimum ammonia concentration to 19% for NOx SNCRs CDs 1007-9 (U1, OS1/OS3/OS5 & OS7/OS8/OS9

Ref.#39). The Department re-stated requirements at U1, OS Summary, Refs #98-106 to reflect new lower limits

from 40 CFR 60 Subpart Cb, effective April 28, 2009. Control device detail sheets were also revised.

New Jersey has elected to integrate its Title I New Source Review (NSR) preconstruction permits with the new Title

V operating permits instead of issuing separate permits. Consequently, the existing preconstruction permit

provisions that were previously approved for this facility have been consolidated into this permit. This permit may

also include applicable requirements for grandfathered sources.

This permit action consolidates previously approved permit terms and conditions into one single permit for the

facility. The New Jersey Department of Environmental Protection (Department) issues this operating permit

authorizing the facility to operate equipment and air pollution control devices. In the operating permit application,

the facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s

application, the Department has approved this operating permit.

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and

emit up to a level specified for each source operation. The signatories named in the application are responsible for

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules.

# Revision 4.0

1/27/09 

# Section B

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

DEFINITIONS

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying

the permit.

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP).

“The EPA,” or “the Administrator,” means the Administrator of the EPA or his designee.

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons.

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons.

“Grandfathered” means, in reference to equipment or co ntrol apparatus, that construction, reconstruction, or

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976,

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or

control apparatus has occurred since.

“Compliance Plan” means the applicable requirements, mo nitoring requirements, record keeping requirements, and

submittal/action requirements detailed in Section J, Facility Specific Requirements, of the operating permit.

# Revision 4.0

1/27/09 

# Section C

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s Potential to Emit (PTE) emissions summary:

Facility Total Potential to Emit

(tons per year)

Primary Secondary Source Categories

VOC

(total) NO

x 

# CO SO 2 

# TSP

(total) Other

(total) PM 10 

# (total) Pb HAPs

(total)

Emission Unit

Summary 83 1260 1660 997 136 133 306 6.57 306

Batch Process

Summary NA NA NA NA NA NA NA NA NA

Non-Source Fugitive

Emissions 1 

# NA NA NA NA NA NA NA NA NA

Group

Summary NA NA NA NA NA NA NA NA NA

Total

Emissions 2 

# 83 1260 1660 997 136 133 306 6.57 306

VOC Volatile Organic Compounds PM 10 

# Particulates under 10 microns

NO

x 

# Nitrogen Oxides Pb Lead

CO Carbon Monoxide HAPs Hazardous Air Pollutants

SO 2 

# Sulfur Dioxide

TSP Total Suspended Particulates

Other Any other air contaminant regulated under the Federal Clean Air Act

1 

# Not applicable to this facility.

2 

# Total emissions from this facility do not include emissions from Insignificant Sources.

# Revision 4.0

1/27/09 

# Section C

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s ha zardous air pollutants (HAP) emissions summary: 3



# HAP TPY

Arsenic 0.067

Beryllium 0.003

Cadmium 0.565

Chromium 0.158

Dioxin TCDD (2,3,7,8) 0.000131

Hydrogen Chloride 284

Hydrogen Fluoride 10.8

Lead 6.57

Mercury 0.14

Nickel 0.043

Polycyclic Organic Matter 3.81

3 

# Do not sum these values for the purpose of establishing a total HAP potential to emit. See previous page for the

allowable total HAP emissions.

# Revision 4.0

1/27/09 

# Section D

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

POLLUTION PREVENTION REPORTING

General Pollution Prevention conditions

The following evaluation requirements are included to track the facility’s progress in several critical areas identified

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with

the air quality standard for the protection of public health . The control of hazardous air pollutants (HAPs) is also a

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels.

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these

air contaminants. Also, as part of significant modification applications, proposed major increases of these air

contaminants requires evaluation of po llution prevention and cross media effects.

The evaluation of these trends requires no increased monito ring. Rather it utilizes existing monitoring data, as

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and

the Department review major source trends periodically, as part of the 5-year renewal review and public comment

process. The Department requests that the facility-wide tr ends be presented on graphs for attachment to the public

information document for the 5-year renewal.

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or

hazardous wastes).

Information to include with the renewal application:

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant

emissions of Volatile Organic Compounds (VOC), Nitr ogen Oxides (NOx), if the facility’s potential to

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or

solid waste) and/or pollution preven tion. Changes should be itemized for each emission unit (or process)

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year

of any HAP. Also, show the net change for the facility.

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a

potential to emit over one ton per year of any HAP. Also, show the net change for the facility.

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject

to reporting under 1 above, on a pound per unit of pr oduct basis, based on annual actual emissions and

annual production over the five year period. Changes should be itemized for each emission unit (or

# Revision 4.0

1/27/09 

# process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton

per year of any HAP. Also, show the net change for the facility.

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP

fugitives, which are subject to reporting under (1) above; explain measures taken to minimize such

fugitives; and provide an explanation for any significant changes.

Information to include with an application for a significant modification to this permit:

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and

HAP air contaminants as part of the significant modifica tion application. If an explanation is provided, the

facility should identify the pollutant and the specific environmental media to which the pollutant is

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to

the air.

# Revision 4.0

1/27/09 

# Section E

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

GENERAL PROVISIONS AND AUTHORITIES

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the

enjoyment of life or property. This shall not include an air contaminant that occurs only in areas over

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations,

including odors, are not considered Federa lly enforceable. [N.J.A.C. 7:27-22.16(g)8]

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be

reported to the Department as follows:

If the air contaminants are released in a quantity or concentration which poses a potential threat to public

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee

shall report the release to the Department:

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the

deviation is identified through source emissions testing, it shall be reported through the source

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall

report the release to the Department as part of th e compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported

through the procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)]

3. The permittee shall comply with all conditions of the operating permit including the approved compliance

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit;

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1]

4. It shall not be a defense for the permittee in an enfo rcement action that it would have been necessary to halt

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit.

[N.J.A.C. 7:27-22.16(g)2]

# Revision 4.0

1/27/09 

# 5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3]

6. The permittee shall furnish to the Department, within a reasonable time, any information that the

Department may request in writing to determine whether cause exists for modifying, revoking and

reissuing, or terminating this operating permit; or to determine compliance with the operating permit.

[N.J.A.C. 7:27-22.16(g)4]

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5]

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C.

7:27-22.16(g)6]

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating

permit to be kept. [N.J.A.C. 7:27-22.16(g)7]

10. The Department and its authorized representatives shall have the right to enter and inspect any facility

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9]

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10]

12. Each permittee shall maintain records of all source em issions testing or monitoring performed at the facility

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained,

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain

all other records required by this operating permit for a period of five years from the date each record is

made. At a minimum, source emission testing or mon itoring records shall contain the information specified

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)]

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department,

on forms provided by the Department, a six month deviation report relating to testing and monitoring

required by the operating permit, not including information for testing and monitoring which have other

reporting schedules specified in the permit. Normally, stack testing reporting is submitted within 45 days

of test completion and continuous monitoring reporting is done quarterly. The six month report must

address other specified monitoring, including, but not limited to, continuous and periodic monitoring data

required by this permit. (See column two and three entitled “Monitoring Requirement” and

“Recordkeeping Requirement,” respectively, in the Facili ty Specific Requirements section of this permit.).

The six month reports for the testing and monitoring performed from January 1 through June 30, shall be

reported by July 30 of the same calendar year; or from July 1 through December 31, shall be reported by

January 30 of the following calendar year. Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports

shall clearly identify all deviations from operating permit requirements, the probable cause of such

deviations, and any corrective actions taken. Any “None” listed in the Submittal/Action Requirement in

the operating permit is not intended to override the six- month deviation report. The report shall be certified

pursuant to N.J.A.C. 7:27-1.39 by a responsible official. Forms provided by the Department can be found

on the Department's website at: http://www.nj.gov/dep/enforcement/compliancecertsair.htm [N.J.A.C.

7:27-22.19(d) 3 and N.J.A.C. 7:27-22.19(e)]

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may

also be considered as your six month deviation report for the period from July 1 through December 31

which is due by January 30 of each year if the annual compliance certification is submitted by January 30.

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but

not limited to NSPS, NESHAP, or MACT.

# Revision 4.0

1/27/09 

# 15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a

provision or condition of the operating permit only if:

i. The violation occurred as a result of an eq uipment malfunction, an equipment start-up or

shutdown, or during the performance of necessary equipment maintenance; and

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)]

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring

protocol during the term of the operating permit. N.J.A.C. 7:27-22.18(j)]

The following paragraphs of this section are included for the permittee's convenience to remind them of their

obligations with certain key applicable requirements. These paragraphs are not enforceable since they paraphrase

areas of the operating permits rule. Also, these paragraphs do not reference all the applicable requirements with

which the permittee must comply.

17. Each owner and each operator of any facility, source operation, or activity to which this permit applies is

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C.

7:27-22.

18. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to

be valid.

19. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate,

calculated as the potential to emit, that exceeds the app licable threshold for reporting emissions set forth in

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating

permit.

20

. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of

this operating permit are met. In the event that there are multiple emission limitations, monitoring,

recordkeeping, and/or reporting requirements for a give n source operation, the facility must comply with all

requirements, including the most stringent.

21. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or

monitoring, to demonstrate compliance with applicable requirements.

22. The permittee shall file a timely and complete application for:

Administrative Amendments;

Seven-Day-Notice changes;

Minor Modifications;

Significant Modifications; and

Renewals.

23. Process monitors must be operated at all times wh en the associated process equipment is operating except

during outage time allowed by Department guidelines/procedures or as outlined in Technical Manual 1005.

The permittee must keep a service log as required.

# Revision 4.0

1/27/09 

# Section F

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

STATE-ONLY APPLI CABLE REQUIREMENTS

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifi cally designate as not being federally enforceable any

permit conditions based only on applicable state requirements. The applicable state requirements to which this

provision applies are listed in the table titled “State-Only Applicable Requirements.”

STATE-ONLY APPLICABLE REQUIREMENTS

The following applicable requirements are not federally enforceable:

SECTION SUBJECT ITEM ITEM # REF. #

E --- 15 ---

G FC --- 3

G FC --- 10

# Revision 4.0

1/27/09 

# Section G

Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

COMPLIANCE PLAN AND INVENTORIES

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN)

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION)

• REASON FOR APPLICATION

• INSIGNIFICANT SOURCE EMISSIONS

• EQUIPMENT INVENTORY

• EQUIPMENT DETAILS

• CONTROL DEVICE INVENTORY

• CONTROL DEVICE DETAILS

• EMISSION POINT INVENTORY

• EMISSION UNIT/BATCH PROCESS INVENTORY

• SUBJECT ITEM GROUP INVENTORY

# Revision 4.0

1/27/09 

# Facility Name: COVANTA ESSEX CO

Program Interest Number: 07736

Permit Activity Number: BOP090001

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

Subject Item and Name Page Number

Facility (FC) :

FC ......................................................................................................................... ....................................... 1

Insignificant Sources (IS):

IS1 – No. 2 Fuel Oil Tanks (<10,000 Gal. Cap.) ............................................................................... ........... 6

IS2 – Fuel Oil Tanks (>10,000 Gal. Cap.) ..................................................................................... ............... 7

Groups (GR) :

GR1 – Equipment subject to NSPS Requirements................................................................................. ....... 9

Emission Units (U):

U1 – Three Municipal Waste Combustors E1, E2 & E3............................................................................ ... 19

U6 – Lime Storage Silo A..................................................................................................... ........................ 76

U7 – Lime Storage Silo B ..................................................................................................... ........................ 76

U8 – Lime Storage Silo C ..................................................................................................... ........................ 76

U9 – Lime Slaker A ........................................................................................................... ........................... 78

U10 – Lime Slaker B .......................................................................................................... .......................... 78

U11 – Activated Carbon Storage Silo .......................................................................................... ................. 79

U12 – Flyash Conditioning Room ............................................................................................... ................. 81

U13 – 7.4 MMBtu/hr Emergency Diesel Generator ................................................................................ ..... 83

U14 – 1.6 MMBtu/hr Emergency Diesel Fire Pump................................................................................ ..... 87

U15 – Ash Conveyance System.................................................................................................. .................. 91

U16 – Abrasive Blaster ....................................................................................................... .......................... 94New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Subject Item:FCRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1General Provisions: Defines numerous termsused in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]None.None.None.2Control and Prohibition of Open Burning:Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]None.None.Obtain an approved permit: Prior tooccurrence of event (prior to open burning).[N.J.A.C. 7:27- 2]3Prohibition of Air Pollution:Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that resultin air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]None.None.None.4Prevention and Control of Air PollutionControl Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]None.None.Comply with the requirement: Uponoccurrence of event. Upon proclamation bythe Governor of an air pollution alert,warning, or emergency, the permittee shallput the Standby Plan into effect. In addition,the permittee shall ensure that all of theapplicable emission reduction objectives ofN.J.A.C. 7:27-12.4, Table I, II, and III arecomplied with whenever there is an airpollution alert, warning, or emergency.[N.J.A.C. 7:27-12]Page 1 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Emission Offsets Rules. [N.J.A.C. 7:27-18]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Comply with the requirement: Uponoccurrence of event. Submit anadministratively complete application whenapplying for a minor modification pursuantto N.J.A.C. 7:27-22.23 or a significantmodification pursuant to N.J.A.C.7:27-22.24. [N.J.A.C. 7:27-22]6Emissions Statements: Submit an annualemission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreedupon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].Submit an Annual Emission Statement:Annually (if required) electronically by May15 or by any mutually agreed upon date, butnot later than June 15 of each year.[N.J.A.C. 7:27-21]7Compliance Certification: Submit annualcompliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]None.None.Submit an Annual Compliance Certification:Annually to the Department and EPA onforms provided by the Department within 60days after the end of each calendar yearduring which this permit was in effect. Theannual compliance certification reportingperiod will cover the calendar year endingDecember 31. Forms provided by theDepartment can be found on theDepartment's web site at the following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]8Prevention of Air Pollution fromArchitectural Coatings and ConsumerProducts. [N.J.A.C. 7:27-23]None.None.None.9For equipment subject to NOx BudgetProgram, comply with N.J.A.C. 7:27-31.[N.J.A.C. 7:27-31]Other: See N.J.A.C. 7:27-31. [N.J.A.C.7:27-31].Other: See N.J.A.C. 7:27-31. [N.J.A.C.7:27-31].Comply with the requirement: Uponoccurrence of event. [N.J.A.C. 7:27-31]10Any operation of equipment which causesoff-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26:2C-19(e)]Other: Observation of plant operations.[N.J.S.A. 26:2C-19(e)].Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A.26:2C-19(e)].Notify by phone: Upon occurrence of event.A person who causes a release of aircontaminants in a quantity or concentrationwhich poses a potential threat to publichealth, welfare or the environment or whichmight reasonably result in citizen complaintsshall immediately notify the Department.Such notification shall be made by callingthe Environmental Action Hotline at (877)927-6337. [N.J.S.A. 26:2C-19(e)]Page 2 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement11Prevention of Significant Deterioration(PSD). [40 CFR 52.21]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Comply with the requirement: Uponoccurrence of event. If subject to PSD, thepermittee shall submit an administrativelycomplete application when applying for asignificant modification pursuant toN.J.A.C. 7:27-22.24. [N.J.A.C. 7:27-22]12National Emission Standards for HazardousAir Pollutants (NESHAPS) for Asbestos.[40 CFR 61]Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 61.145 and 61.150when conducting any renovation ordemolition activities at the facility. [40 CFR61]13Protection of Stratospheric Ozone:1) If thepermittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 82 Subparts A, B, E,F, and G. [40 CFR 82]Page 3 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement14Deviation Report: In accordance withN.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department, onforms provided by the Department, acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7.27-22.19(d)3, N.J.A.C.7.27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]None.Other: The permittee shall maintaindeviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].Submit a report: As per the approvedschedule. The six-month reports for otherspecified testing or monitoring required bythe operating permit performed fromJanuary 1 through June 30 shall besubmitted by July 30 of the same calendaryear, and from July 1 through December 31,shall be submitted by January 30 of thefollowing calendar year. The report shall besubmitted to the Regional EnforcementOffice and shall be certified pursuant toN.J.A.C. 7:27-1.39 by the responsibleofficial. Forms provided by the Departmentcan be found on the Department's web site atthe following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]15No person shall combust used oil except asauthorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]None.None.Comply with the requirement: Prior tooccurrence of event (prior to burning usedoil) either register with the Departmentpursuant to N.J.A.C. 7:27-20.3 or obtain apermit issued by the Department pursuantto N.J.A.C. 7:27-8 or 7:27-22, whichever isapplicable. [N.J.A.C. 7:27-20.2(d)]Page 4 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement16Prevention of Accidental Releases: Facilitiesproducing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]Other: Comply with 40 CFR 68. [40 CFR68].Other: Comply with 40 CFR 68. [40 CFR68].Other (provide description): Other. Complywith 40 CFR 68 as described in theApplicable Requirement. [40 CFR 68]17For equipment subject to Clean AirInterstate Rule (CAIR) NOx TradingProgram, comply with N.J.A.C. 7:27-30.[N.J.A.C. 7:27-30]Other: See N.J.A.C. 7:27-30. [N.J.A.C.7:27-30].Other: See N.J.A.C. 7:27-30. [N.J.A.C.7:27-30].Comply with the requirement: Uponoccurrence of event. [N.J.A.C. 7:27-30]18For equipment subject to CO2 BudgetTrading Program, comply with N.J.A.C.7:27C. [N.J.A.C. 7:27C]Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Comply with the requirement: Uponoccurrence of event. [N.J.A.C. 7:27C]Page 5 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Subject Item:IS1 No. 2 Fuel Oil Tanks (<10,000 Gallons Capacity)Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The maximum allowable distillate fuel oilsulfur content is based on the geographiclocation of the facility (Essex County).Sulfur Content in Fuel <= 0.2 %. [N.J.A.C.7:27- 9.2(b)]None.None.None.2The vapor pressure of the liquid, excludingthe vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]None.None.None.Page 6 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Subject Item:IS2 Fuel Oil Tank (>10,000 Gallons Capacity)Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The maximum allowable distillate fuel oilsulfur content is based on the geographiclocation of the facility (Essex County).Sulfur Content in Fuel <= 0.2 %. [N.J.A.C.7:27- 9.2(b)]None.None.None.2The operating temperature shall not begreater than 350 degrees F. [N.J.A.C.7:27-22.1]None.None.None.3The vapor pressure of the liquid, excludingthe vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]None.None.None.4The tank or vessel shall have no visibleemissions, exclusive of water vapor, to theoutdoor atmosphere. [N.J.A.C. 7:27-22.1]None.None.None.5The tank or vessel shall not emit any aircontaminants which may cause an odordetectable outside the property boundariesof the facility. [N.J.A.C. 7:27-22.1]None.None.None.6The tank or vessel shall not be subject to anyNESHAPS, MACT, or NSPS air pollutioncontrol standards, excluding the NSPSrequirements to maintain a record of thecontents of the tank or vessel, the period ofstorage of these contents, and the maximumtrue vapor pressure of the liquid stored.[N.J.A.C. 7:27-22.1]None.None.None.7The tank's or vessel's potential to emit eachTXS and each HAP does not exceed the deminimus reporting thresholds as specified inN.J.A.C. 7:27-22, Appendix. [N.J.A.C.7:27-22.1]None.None.None.8The percentage by weight of all HAPscollectively in the raw material stored in thetank, or mixed or blended in the vessel, isless than 1.0 percent. [N.J.A.C. 7:27-22.1]None.None.None.Page 7 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9The owner or operator shall have readilyavailable upon Department request astatement certified in accordance withN.J.A.C. 7-27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank or vesselmeets the applicable requirement and (3)attests that the tank or vessel is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]None.None.None.Page 8 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Subject Item:GR1 Equipment Subject to Federal NSPS RequirementsRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1For equipment subject to NSPS (E1, E2, E3,E16, E17 and E18), all requests, reports,applications, submittals, and othercommunications to the Administratorpursuant to Part 60 shall be submitted induplicate to the Regional Office of USEnvironmental Protection Agency. Submitinformation to: Region II, Director, Air andWaste Management Division, USEnvironmental Protection Agency, 21stFloor, 290 Broadway, New York, NY10007. [40 CFR 60.4(a)]None.None.Submit a report: As per the approvedschedule to EPA Region II as required by 40CFR 60. [40 CFR 60.4(a)]2For equipment E1, E2, E3, E16, E17 andE18, copies of all information submitted toEPA pursuant to 40 CFR Part 60, must alsobe submitted to the appropriate RegionalEnforcement Office of NJDEP. [40 CFR60.4(b)]None.None.Submit a report: As per the approvedschedule to the appropriate RegionalEnforcement Office of NJDEP as requiredby 40 CFR 60. [40 CFR 60.4(b)]Page 9 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3The owner or operator subject to theprovisions of 40 CFR Part 60 (equipmentE1, E2, E3, E16, E17 and E18) shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of any physical or operationalchange to an existing facility which mayincrease the emission rate of any airpollutant to which a standard applies, unlessthat change is specifically exempted underan applicable subpart or in section 60.14(e).The notification shall include informationdescribing the precise nature of the change,present and proposed emission controlsystems, productive capacity of facilitybefore and after the change and the expectedcompletion date of the change. Notificationshall be postmarked within 60 days or assoon as practicable before any change iscommenced. The Administrator mayrequest additional relevant informationsubsequent to this notice. [40 CFR60.7(a)(4)]None.None.Submit notification: Upon occurrence ofevent to EPA Region II and the appropriateRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7 [40 CFR60.7(a)(4)]4For equipment E1, E2, E3, E16, E17 andE18, the owner or operator shall maintainrecords of the occurrence and duration ofany startup, shutdown, or malfunction in theoperation of an affected facility, anymalfunction of air pollution controlequipment or any periods during whichcontinuous monitoring system or monitoringdevice is inoperative. [40 CFR 60.7(b)]None.Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event , or manually in apermanently bound logbook. The recordsshould be kept in a permanent form suitablefor inspections. [40 CFR 60.7(b)]None.Page 10 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5For equipment E1, E2 and E3, each owneror operator required to install a continuousmonitoring device shall submit an excessemissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see section 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the Administrator, on acase-by-case basis, determines that morefrequent reporting is necessary to accuratelyassess the compliance status of the source.All reports shall be postmarked by the 30thday following the end of each six-monthperiod. [40 CFR 60.7(c)]None.Other: Written records of excess emissionsshall include the following information: (1)The magnitude of excess emissionscomputed in accordance with section60.13(h), any conversion factor(s) used, andthe date and time of commencement andcompletion of each time period and excessemissions. The process operating timeduring the reporting period. (2) Specificidentification of each period of excessemissions that occurs during startups,shutdowns, and malfunctions of the affectedfacility. The nature and cause of anymalfunction (if known), the corrective actiontaken or preventative measures adopted. (3)The date and time identifying each periodduring which the continuous monitoringsystem was inoperative except for zero andspan checks and the nature of the systemrepairs or adjustments. (4) When no excessemissions have occurred or the continuousmonitoring system(s) have not beeninoperative, repaired, or adjusted, suchinformation shall be stated in the report.[40CFR 60.7(c)].Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Semi-annually on January 31 andJuly 31 of each year. Additionally, thereport shall be submitted to the EPA RegionII Administrator and be in the formatspecified at 40 CFR 60.7(c) and 40 CFR60.7(d). Written reports of excess emissionsshall include all the information included inthe written records listed underrecordkeeping requirement of this applicablerequirement. [40 CFR 60.7(c)]Page 11 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6For equipment subject to NSPS CMSrequirements (E1, E2 and E3): Each owneror operator required to install a continuousmonitoring device shall submit an excessemissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see section 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the Administrator, on acase-by-case basis, determines that morefrequent reporting is necessary to accuratelyassess the compliance status of the source.All reports shall be postmarked by the 30thday following the end of each six-monthperiod. [40 CFR 60.7(c)]None.Other: Written records of excess emissionsshall include the following information: (1)The magnitude of excess emissionscomputed in accordance with section60.13(h), any conversion factor(s) used, andthe date and time of commencement andcompletion of each time period and excessemissions. The process operating timeduring the reporting period. (2) Specificidentification of each period of excessemissions that occurs during startups,shutdowns, and malfunctions of the affectedfacility. The nature and cause of anymalfunction (if known), the corrective actiontaken or preventative measures adopted. (3)The date and time identifying each periodduring which the continuous monitoringsystem was inoperative except for zero andspan checks and the nature of the systemrepairs or adjustments. (4) When no excessemissions have occurred or the continuousmonitoring system(s) have not beeninoperative, repaired, or adjusted, suchinformation shall be stated in the report.[40CFR 60.7(c)].Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Semi-annually beginning on the30th day of the 6th month following initialperformance tests. The report shall bepostmarked by the 30th day following theend of each six-month period. The reportshall be submitted to the EPA Region IIAdministrator and the RegionalEnforcement Office of NJDEP and be in theformat specified at 40 CFR Part 60.7(c) and40 CFR Part 60.7(d). Written reports ofexcess emissions shall include all theinformation included in the written recordslisted under recordkeeping requirement ofthis applicable requirement. [40 CFR60.7(c)]7For equipment E1, E2 and E3, the owner oroperator shall conduct performance tests anddata reduction in accordance with the testmethods and procedures contained ineachapplicable subpart, unless otherwisespecified and approved by theAdministrator. [40 CFR 60.8(b)]None.None.None.8For equipment E1, E2 and E3, performancetests shall be conducted under conditions theAdministrator specifies to the plant operatorbased on representative performance of theaffected facility. Operations during periodsof startup, shutdown and malfunction shallnot constitute representative conditions forthe purpose of the performance test nor shallemissions in excess of the level of theapplicable emission limit be considered aviolation of the applicable emission limitunless otherwise specified in the applicablestandard. [40 CFR 60.8(c)]None.None.None.Page 12 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9For equipment E1, E2 and E3, the owner oroperator shall provide the Administrator atleast 30 days prior notice of anyperformance test and shall provide adequateperformance testing facilities as specified in40 CFR Part 60.8(e). [40 CFR 60.8(d)]None.None.None.10For equipment E1, E2 and E3, unlessotherwise specified in the applicablesubpart,each performance test shall consistof three separate runs using the applicabletest method. [40 CFR 60.8(f)]None.None.None.11For equipment E1, E2 and E3, compliancewith NSPS standards specified in thispermit, other than opacity, shall bedetermined only by performance testsestablished by 40 CFR 60.8, unlessotherwise specified in NSPS. [40 CFR60.11(a)]None.None.None.12For equipment required to conduct visualopacity tests (E16 and E17): The owner oroperator shall demonstrate compliance withNSPS opacity standards specified in 40 CFRPart 60, unless otherwise specified andapproved by the Administrator. [40 CFR60.11(b)]Monitored by visual determination annually,based on 6 minute blocks. Compliance withfugitive ash emission limits shall be basedon a series of three one hour observations,performed annually, using EPA ReferenceMethod 22. This is based on therequirement at 40 CFR 60.58b(k). [40 CFR60.39b(d)]&. [40 CFR 60.11(b)]Recordkeeping by data acquisition system(DAS) / electronic data storage annually , ormanually in a permanently bound logbook.The owner or operator shall maintainrecords of opacity of emissions based onMethod 9 observations. [40 CFR 60.13(h)]Submit a report: Annually. The owner oroperator shall submit results of Method 9observation data to the Administrator. [40CFR 60.11(e)(2)]13For equipment subject to the NSPS COMrequirement (E1, E2, and E3), the owner oroperator shall demonstrate compliance withNSPS opacity standards specified in 40 CFRPart 60. [40 CFR 60.11(b)]None.None.None.14For equipment E1, E2, E3, E16, E17 andE18, the NSPS opacity standard shall applyat all times except during periods of startup,shutdown, malfunctions and as otherwisespecified in this permit. [40 CFR 60.11(c)]None.None.None.Page 13 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15At all times, including periods of start-up,shutdown, and malfunction, owners andoperators shall, to the extent practicable,maintain and operate any affected facility(equipment E1, E2, and E3), includingassociated air pollution control equipment ina manner consistent with good air pollutioncontrol practice for minimizing emissions.Determination of whether acceptableoperating and maintenance procedures arebeing used will be based on informationavailable to the Administrator which mayinclude, but is not limited to, monitoringresults, opacity observations, review ofoperation and maintenance procedures, andinspection of the source. [40 CFR 60.11(d)]None.None.None.16No owner or operator subject to NSPSstandards in Part 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to the atmosphere.[40 CFR 60.12]None.None.None.Page 14 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement17Opacity: For equipment E1, E2, and E3, theowners and operators of a COMS installedin accordance with the provisions of 40 CFR60, must automatically, intrinsic to theopacity monitor, check the zero and upscale(span) calibration drifts at least once daily.For a particular COMS, the acceptable rangeof zero and upscale calibration materials isas defined in the applicable version of PS-1in appendix B of this part. For a COMS, theoptical surfaces, exposed to the effluentgases, must be cleaned before performingthe zero and upscale drift adjustments,except for systems using automatic zeroadjustments. The optical surfaces must becleaned when the cumulative automatic zerocompensation exceeds 4 percent opacity. [40CFR 60.13(d)(1)]None.Opacity: Recordkeeping by ecords inaccordance with 40 CFR 60.7(f). [40 CFR60.13(d)].None.18Opacity: Unless otherwise approved by theAdministrator, the following proceduresmust be followed for a COMS. Minimumprocedures must include an automatedmethod for producing a simulated zeroopacity condition and an upscale opacitycondition using a certified neutral densityfilter or other related technique to produce aknown obstruction of the light beam. Suchprocedures must provide a system check ofall active analyzer internal optics with poweror curvature, all active electronic circuitryincluding the light source and photodetectorassembly, and electronic orelectro-mechanical systems and hardwareand or software used during normalmeasurement operation. [40 CFR60.13(d)(2)]None.Opacity: Recordkeeping by ecords inaccordance with 40 CFR 60.7(f). [40 CFR60.13(d)].None.Page 15 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement19Except for system breakdowns, repairs,calibration checks, and zero and spanadjustments, all continuous opacitymonitoring systems shall be in continuousoperation for equipment E1, E2, and E3.They shall complete a minimum of one cycleof sampling and analyzing for eachsuccessive 10-second period and one cycleof data recording for each successive6-minute period. [40 CFR 60.13(e)(1)]Other: See Applicable Requirement. [40CFR 60.13(e)(1)].Other: See Applicable Requirement. [40CFR 60.13(e)(1)].None.20Except for system breakdowns, repairs,calibration checks, and zero and spanadjustments, all continuous monitoringsystems measuring emissions except opacityshall be in continuous operation forequipment E1, E2, and E3. They shallcomplete a minimum of one cycle ofoperation (sampling, analyzing and datarecording) for each successive 15-minuteperiod. [40 CFR 60.13(e)(2)]Other: See Applicable Requirement. [40CFR 60.13(e)(2)].Other: See Applicable Requirement. [40CFR 60.13(e)(2)].None.21All continuous monitoring systems ormonitoring devices shall be installed suchthat representative measurements ofemissions or process parameters from theaffected facility (equipment E1, E2, and E3)are obtained. Procedures for location ofcontinuous monitoring systems contained inthe applicable Performance Specifications ofAppendix B of 40 CFR Part 60 shall beused. [40 CFR 60.13(f)]None.None.None.Page 16 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement22For equipment E1, E2, and E3, the owner oroperator shall reduce all continuousmonitoring systems for measuring opacitydata to 6-minute averages which shall becalculated from 36 or more data pointsequally spaced over each 6-minute period.Data recorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmeticor integrated average of all data may beused. The data may be recorded in reducedor nonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]None.Other: See Applicable Requirement. [40CFR 60.13(h)].None.Page 17 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement23For equipment E1, E2, and E3, the owner oroperator shall reduce all continuousmonitoring systems (other than opacity) datato 1-hour averages which shall be computedfrom four or more data points equallyspaced over each 1-hour period. Datarecorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmeticor integrated average of all data may beused. The data may be recorded in reducedor nonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]None.Other: See Applicable Requirement. [40CFR 60.13(h)].None.24Changes in time periods for submittal ofinformation and postmark deadlines set forthin this subpart, may be made only uponapproval by the Administrator and shallfollow procedures outlined in 40 CFR Part60.19. [40 CFR 60.19]None.None.None.Page 18 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U1 Municipal Waste Combustors (E1, E2 & E3) - Subject to NSPS Subparts Cb and 40 CFR 62 Subpart FFFOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1STACK TESTING REQUIREMENTS:All testing required in the followingconditions must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable standards, butwithout creating an unsafe condition, frommodification BOP080002. [N.J.A.C.7:27-22.16(a)]None.None.None.2STACK TESTING REQUIREMENTS:Conduct annual stack tests oneachmunicipal solid waste combustor todemonstrate compliance with the lead andcadmium emission limits. Stack testing is asrequired at 40 CFR 60.58b(d).[N.J.A.C. 7:27-22.16 (o)], [40 CFR60.39b(d) & (f)] & [40 CFR 62.14109(b)]Monitored by stack emission testingannually, based on the average of three tests(as a minimum.) Stack testing for lead andcadmium (using EPA Method 29) shall beas required at 40 CFR 60.58b(d)(1).[N.J.A.C. 22.16(o)], [40 CFR 60.39b(d) &(f)] &. [40 CFR 62.14109(b)]Recordkeeping by stack test results annuallyAll records shall be maintained onsite ineither paper copy or computer-readableformat. This is as indicated in 40 CFR60.59b(d)(9)(i) and 40 CFR 60.59b(d)(k).[N.J.A.C. 7:27-22.16(o)], [40 CFR60.39b(d) & (f)] &. [40 CFR 62.14109(a)]Stack Test - Submit protocol, conduct testand submit results: Annually. For all tests,the permittee must contact BTS at609-530-4041 to schedule a mutuallyacceptable test date which shall be no laterthan one year after the previous test. Stacktest reports must be submitted to BTS within45 days after performing the stack testpursuant to N.J.A.C. 7:27-22.19(d). The testresults must be certified by a licensedprofessional engineer or certified industrialhygienist.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed).As indicated in 40 CFR 59b(g)(1), a list ofthe emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.18(e)],[N.J.A.C. 7:27-22.18(h)], [40 CFR60.39b(d) & (f)], &. [40 CFR 62.14109(a)]OS SummaryPage 19 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3STACK TESTING REQUIREMENTS:Conduct annual stack testseach municipalsolid waste combustor to determinecompliance with HCl emission limits.[N.J.A.C. 7:27-22.16(e)], [40 CFR60.39b(f)] & [40 CFR 62.14109(b)]Monitored by stack emission testingannually, based on any 60 minute period todetermine compliance with emission limitspursuant to N.J.A.C. 7:27-22.16(e), and theaverage of a mimimum of three tests todetermine compliance with emission limitspursuant to 40 CFR 60.39b(f) and 40 CFR62.14103(b)(2). Stack testing for HCl(using EPA Method 26 or 26A) shall satisfythe requirements at 40 CFR 60.58b(f).[N.J.A.C. 7:27-22.16(e)], 40 CFR 60.39b(f),&. [40 CFR 62.14109(b)]Recordkeeping by stack test results annuallyAll records shall be maintained onsite ineither paper copy or computer-readableformat. This is as indicated in 40 CFR60.59b(d)(9)(i) and 40 CFR 60.59b(d)(k).[N.J.A.C. 7:27-22.16(o)], [40 CFR60.39b(f)] &. [40 CFR 62.14109(a)]Stack Test - Submit protocol, conduct testand submit results: Annually. The permitteemust contact BTS at 609-530-4041 toschedule a mutually acceptable test datewhich shall be no later than one year afterthe previous test. Stack test reports must besubmitted to BTS within 45 days afterperforming the stack test pursuant toN.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a licensed professionalengineer or certified industrial hygienist.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed).As indicated in 40 CFR 59b(g)(1), a list ofthe emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(f) and 40 CFR 14109(a).[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(f)], &. [40CFR 62.14109(a)]Page 20 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4STACK TESTING REQUIREMENTS:Conduct annual stack tests fordioxins/furans. Total polychlorinateddibenzodioxins emissions and totalpolychlorinated dibenzofurans(dioxins/furans) must be measured usingEPA Reference Method 23. This is asindicated at 40 CFR 60.59b(g)(3). [N.J.A.C.7:27-22.16(o)], [40 CFR 60.39b(d)]& [40CFR 62.14109(b)]Monitored by stack emission testingannually, based on the average of three tests.Minumum sample time shall be 4 hours perrun, using EPA Test Method 23 specified at40 CFR 60.58b(g)(3) & (5), except that:Where all performance tests over a 2-yearperiod indicate that dioxin/furan emissionsare <= 15 ng/dscm corrected to 7% O2 (totalmass) for all units, the facility may elect toconduct annual performance tests in one unitper year. At a minimum, a performance testfor dioxin/furan emissions shall beconducted annually (no more than 12months following the previous performancetest) on one unit. Each year a different unitshall be tested, and the units shall be testedin sequence (e.g., unit 1, unit 2, unit 3) aslong as each test indicates an emission levelless than or equal to 15 ng/dscm (totalmass). If test indicates a dioxin/furanemission level greater than 15 ng/dscmcorrected to 7% O2 (total mass),performance tests thereafter shall beconducted annually on all units until andunless all annual performance tests for allunits over a 2-year period indicate adioxin/furan emission level less than orequal to 15 ng/dscm corrected to 7% O2(total mass). [N.J.A.C. 7:27-22.16(o)], [40CFR 60.39b(d)], [40 CFR 62.14109(b)] &.[40 CFR 62.14109(d)(1)]Recordkeeping by stack test results annuallyAll records shall be maintained onsite ineither paper copy or computer-readableformat. This is as specified at 40 CFR60.59b(d)(9)(i) and 40 CFR 60.59b(k).[N.J.A.C. 22.16(o)], [40 CFR 60.39b(d)] &.[40 CFR 62.14109(a)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. The permittee must contact BTSat 609-530-4041 to schedule a mutuallyacceptable test date which shall be no laterthan one year after the previous test. Stacktest reports must be submitted to BTS within45 days after performing the stack testpursuant to N.J.A.C. 7:27-22.19(d). The testresults must be certified by a licensedprofessional engineer or certified industrialhygienist.Test results shall report lbs/hour, lbs/MMBtu, ppm, ng/dscm (as needed). Emissionrates of each congener which contains 4 ormore chlorine atoms shall be reported.As indicated in 40 CFR 59b(g)(1), a list ofthe emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.16(o)],[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)], &. [40 CFR 62.14109(a)]Page 21 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5STACK TESTING REQUIREMENTS:Conduct annual stack tests oneachmunicipal solid waste combustor todemonstrate compliance with the particulateemission limits, by:i. Three test runs using EPA ReferenceMethod 5;ii. Three test runs using the New JerseyTest Method for incinerators (as required bythe test method, paticulate matter shallinclude solid and liquid particles, excludingwater, collected in the "front half" and the"back half" of the sampling train), andiii. Three test runs for PM-10 (includingback half condensibles).[N.J.A.C. 7:27-22.16(a)], [N.J.A.C.7:27-22.16(e)], [40 CFR 60.39b(d)]& [40CFR 62.14109(b)]Monitored by stack emission testingannually, based on the average of three testsconducted successively. Compliance withall TSP emission limits (except for the limitwhich stipuates boiler soot blowing)pursuant to N.J.A.C. 7:27-22.16(e) and 40CFR 62.14103(a)(1) shall be determined byeach of three EPA Method 5 test runsindicated in (i) of the applicablerequirement, as required in thepreconstruction permit and 40 CFR60.58b(c). Compliance with the emissionlimit pusuant to N.J.A.C. 7:27-11 shall bedetermined from the worst-case runindicated in (ii) of the applicablerequirement. Compliance with the PM-10limit stipulated under N.J.A.C.7:27-22.16(e) will be determined from thefront and back-half of the PM-10 train bythe average of the three EPA method 201Aand 202 test runs indicated in (iii) of theapplicable requirement. [ N.J.A.C.7:27-22.16(a)], [N.J.A.C. 7:27-22.16(e)],[40 CFR 60.39b(d)] and. [40 CFR62.14109(b)]Recordkeeping by stack test resultsannually. All records shall be maintainedonsite in either paper copy orcomputer-readable format. This is asspecified at 40 CFR 60.59b(d)(9)(i) and 40CFR 60.59b(k). [N.J.A.C. 22.16(e)], [40CFR 60.39b(d)] and. [40 CFR 62.14109(a)]Submit a stack test report: Annually. Forall tests, the permittee must contact BTS at609-530-4041 to schedule a mutuallyacceptable test date which shall be no laterthan one year after the previous test. Stacktest reports must be submitted to BTS within45 days after performing the stack testpursuant to N.J.A.C. 7:27-22.19(d). The testresults must be certified by a New Jerseylicensed professional engineer or certifiedindustrial hygienist.Test results shall report lbs/hour, gr/dscf,ppm (as needed).As indicated in 40 CFR 60.59b(g)(1), a listof the emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.16(o)],[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)], and. [40 CFR 62.14109(a)]Page 22 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6STACK TESTING REQUIREMENTS: Thepermittee shall conduct stack emissiontesting for mercury on each municipal solidwaste combustor to satisfy the requirementsunder N.J.A.C. 7:27-22.16(e), N.J.A.C.7:27-27.4 and 40 CFR 60.58b(d)(2).[N.J.A.C. 7:27-22.16(e)], [N.J.A.C.7:27-27.4], [40 CFR 60.39b(d)], & [40 CFR62.14109(b)]Monitored by stack emission testingannually, based on the average of threeDepartment validated stack test runs usingEPA Reference Method 29. The tests formercury shall consist of a minimum of threesource emission tests to measure mercury inthe gas stream at the inlet of the air pollutioncontrol apparatus serving each combustionunit, and simultaneously perform threesource emission tests to measure mercury inthe gas stream at the exit of the controlapparatus. If source emission testing failsto demonstrate compliance with theapplicable requirement, then the frequencyof source testing shall increase to threesource emission tests quarterly. In this case,there shall be at least a 45 calendar dayinterval between the testing performed for agiven quarter and the testing performed forthe preceding quarter, unless a shorterperiod is approved by the Department. Ifcompliance with the applicable requirementis then achieved and maintained during twoconsecutive years, the permittee may againreduce the frequency of source emissiontesting from three source emission testsperformed quarterly to three source emissiontests performed annually, not necessarily inthe first quarter of each calendar year (frommodification BOP080002.) Testing shallalso satisfy the requirements at 40 CFR 60.58b(d)(2), which requires annual testing.[N.J.A.C. 7:27-27.4(c)], [40 CFR60.39b(d)]&. [40 CFR 62.14109(b)]Recordkeeping by stack test results at theapproved frequency. All records shall bemaintained onsite in either paper copy orcomputer-readable format. This is asindicated in 40 CFR 60.59b(d)(9)(i) and 40CFR 60.59b(d)(k). [N.J.A.C.7:27-22.16(o)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)] &. [40 CFR 62.14109(a)]Submit a stack test report: As per theapproved schedule. For all annual tests, thepermittee must contact BTS at609-530-4041 to schedule a mutuallyacceptable test date which shall be no laterthan one year after the previous test. Stacktest reports must be submitted to BTS within45 days after performing the stack testpursuant to N.J.A.C. 7:27-22.19(d). The testresults must be certified by a licensedprofessional engineer or certified industrialhygienist.Test results shall report lbs/hour, ug/dscm,as needed.As indicated in 40 CFR 59b(g)(1), a list ofthe emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.16(o)],[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)], &. [N.J.A.C. 7:27-27.4(f)]Page 23 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7STACK TESTING REQUIREMENTS:Conduct comprehensive stack tests oneachmunicipal solid waste combustor within oneyear prior to renewal of this operatingpermit, to demonstrate compliance with theSO2, nitrogen oxides, SO3 + H2SO4 (asconverted and expressed as H2SO4),Volatile Organic Compounds (VOC),Arsenic, Beryllium, Chromium, Nickel,Ammonia, and TCDD (2,3,7,8-) emissionlimits. In addition, tests for polycyclicaromatic hydrocarbons (or polycyclicorganic matter), Benzo (A) Pyrene, carbontetrachloride, formaldehyde,perchloroethylene (tetrachloroethylene),trichloroethylene and vinyl chlorideemissions must be conducted. [Frommodification BOP080002.] [N.J.A.C.7:27-22.16(a)]Monitored by stack emission testing prior topermit renewal, based on the average ofthree Department validated stack test runs.Stack test shall be conducted for SO2,nitrogen oxides, SO3+H2SO4 (as convertedand expressed as H2SO4), VOC, Ammonia,Arsenic, Beryllium, Chromium, Nickel, andTCDD (2,3,7,8-) emission limits. Inaddition, tests for polycyclic aromatichydrocarbons (or polycyclic organic matter),Benzo (A) Pyrene, carbon tetrachloride,formaldehyde, perchloroethylene(tetrachloroethylene), trichloroethylene andvinyl chloride emissions must be conducted.This is based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Recordkeeping by stack test results every 5years based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Submit a stack test report: As per theapproved schedule (before one year prior torenewal of this operating permit.) Stacktesting shall be performed using approvedprotocols. For all tests, the permittee mustcontact BTS at 609-530-4041 to schedule amutually acceptable test date which shall beno later than five years after the previoustest. Stack test reports must be submitted toBTS within 45 days after performing thestack test pursuant to N.J.A.C.7:27-22.19(d). The test results must becertified by a licensed professional engineeror certified industrial hygienist.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed) [N.J.A.C.7:27-22.18(e)] &. [N.J.A.C. 7:27-22.18(h)]8STACK TESTING REQUIREMENTS:Perform stack tests on each municipal solidwaste combustor to demonstrate compliancewith the 1-hour CO and HF emission limitswithin one year prior to renewal of thisoperating permit. [From modificationBOP080002.] [N.J.A.C. 7:27-22.16(a)]Monitored by stack emission testing every 5years, based on any 60 minute period usingEPA Method 10 for CO and EPA Method13A for HF, or methods approved by theDepartment and EPA, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Recordkeeping by stack test results every 5years based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Submit a stack test report: As per theapproved schedule (before one year prior torenewal of this operating permit.) Stacktesting shall be performed using approvedprotocols. For all tests, the permittee mustcontact BTS at 609-530-4041 to schedule amutually acceptable test date which shall beno later than five years after the previoustest. Stack test reports must be submitted toBTS within 45 days after performing thestack test pursuant to N.J.A.C.7:27-22.19(d). The test results must becertified by a licensed professional engineeror certified industrial hygienist.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed) [N.J.A.C.7:27-22.18(e)] &. [N.J.A.C. 7:27-22.18(h)]9These municipal waste incinerators are eachsubject to the 40 CFR 60 Subpart CbEmission Guidelines and Compliance Timesfor Large Municipal Waste Combustors thatwere Constructed on or Before September20, 1994. Compliance with all applicableportions of this regulation is required. [40CFR 60.32(b)]None.None.None.Page 24 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10The operating practices in this OP shall be atleast as protective as those requirementslisted in 40 CFR 60.53b(b) and (c) ofsubpart Eb [40 CFR 60.35b]None.None.None.11The municipal waste combustor operatortraining and certification shal be at least asprotective as those requirements listed in 40CFR 60.54b of subpart Eb. The compliancewith these requirements shall be accordingto the schedule specified in 40 CFR60.39b(c)(4). [40 CFR 60.35b]None.None.None.12Municipal waste combustor fugitive ashemissions shall be at least as protective asthose requirements listed in 40 CFR 60.55bof subpart Eb. [40 CFR 60.36b]None.None.None.13This OP shall include performance testingmethods listed in 40 CFR 60.58b subpartEb, as applicable, except as provided forunder 40 CFR 60.24(b)(2) of subpart B andparagraphs 38b(b).Reporting and recordkeeping provisionslisted in 40 CFR 60.59b of subpart Eb, asapplicable, except for the sitingrequirements under 40 CFR 60.59b(a),(b)(5), and (d)(11) of subpart Eb. [40 CFR60.38b(a)]None.None.None.Page 25 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement14This OP shall include compliance schedulesfor meeting the revised April 28, 2009emission limits in 40 CFR 60.33b(a), (c),and (d) and the revised testing provisions in40 CFR 60.38b(b) [Where all performancetests over a 2-year period indicate thatdioxin/furan emissions are less than or equalto 15 nanograms per dry standard cubicmeter (total mass) for all affected facilitieslocated within a municipal waste combustorplant](1) Compliance with the revised April28, 2009 emission limits is required asexpeditiously as practicable, but no laterthan April 28, 2009, except as provided inparagraph (2) below.(2) The owner or operator of an affectedfacility who is planning an extensiveemission control system upgrade maypetition the Administrator for a longercompliance schedule and must demonstrateto the satisfaction of the Administrator theneed for the additional time. If approved, theschedule may exceed the schedule inparagraph (1) above, but cannot exceed May10, 2011. [40 CFR 60.39b(g)]None.None.None.15The facility is not subject to the nitrogenoxide standards in the NSPS for industrialboilers (40 CFR, Part 60, Subpart Db) sinceany facility covered by an EPA approvedState or Federal section 111(d)/129 planimplementing Subpart Cb or subpart BBBBof this part is not covered by subpart Db.[40 CFR 60.40b(l)]None.None.None.16These municipal waste incinerators meetingthe applicability requirements under section40 CFR 60.32b are not subject to subpart Eof 40 CFR 60 in accordance with the finalrule (Subpart Cb) dated May 10, 2006 (at 71FR 27333.) [40 CFR 60.32b(n)]None.None.None.Page 26 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement17The facility is not subject to the NESHAPfor beryllium (40 CFR Part 61, Subpart C),and shall not accept any berylliumcontaining waste as defined in 40 CFR61.31(g). [N.J.A.C. 7:27-22.16(e)]Other: Waste contents. Per delivery.[N.J.A.C. 7:27-22.16(a)].Other: Waste manifests. Per Delivery.[N.J.A.C. 7:27-22.16(o)].None.18The three municipal solid waste units aresubject to the emission guidelines codifiedat 40 CFR 62 Subpart FFF, Federal PlanRequirements for Large Municipal WasteCombustors Constructed on or BeforeSeptember 20, 1994. Compliance with allapplicable portions of these Subparts isrequired. [40 CFR 62.14100]None.None.None.19Particulate Emissions <= 42.3 lb/hr.Maximum emission rate for each MWCfrom the table at N.J.A.C. 7:27-4.2(a), basedon the Maximum Gross Heat input.Emission limit applies at all times, includingstartup and shutdown. [N.J.A.C. 7:27-4.2(a)]None.None.None.20SO2 <= 2,000 ppmv at standard conditions.Emission limit applies at all times, includingstartup and shutdown. [N.J.A.C. 7:27-7.2(b)1]None.None.None.21SO2 <= 1,100 lb/hr foreach MWC (in any60-minute period), based on the calculationprocedure at N.J.A.C. 7:27-7.2(r). Emissionlimit applies at all times, including startupand shutdown. [N.J.A.C. 7:27- 7.2(b)2]None.None.None.22SO2 <= 2,200 lb/hr foreach MWC at anyinstant, based on the calculation procedureat N.J.A.C. 7:27-7.2(r). Emission limitapplies at all times, including startup andshutdown. [N.J.A.C. 7:27- 7.2(b)2]None.None.None.23SO3 and H2SO4, as converted andexpressed as H2SO4 <= 10 mg/ft^3 atstandard conditions. Emission limit appliesfor each MWC at all times, including startupand shutdown. [N.J.A.C. 7:27- 7.2(g)1]None.None.None.Page 27 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement24SO3 and H2SO4, as converted andexpressed as H2SO4 <= 260 lb/hr in any60-minute period, based on the calculationprocedure at N.J.A.C. 7:27-7.2(r). Emissionlimit applies at all times, including startupand shutdown. Emission limit applies at alltimes for each MWC, including startup andshutdown. [N.J.A.C. 7:27- 7.2(g)2]None.None.None.25SO3 and H2SO4, as converted andexpressed as H2SO4 <= 520 lb/hr at anyinstant, based on the calculation procedureat N.J.A.C. 7:27-7.2(r). Emission limitapplies at all times for each MWC,including startup and shutdown. [N.J.A.C.7:27- 7.2(g)2]None.None.None.26SO2 <= 0.3 lb/MMBTU. No person shalluse solid fuel whose combustion causessulfur dioxide (SO2) emissions from anystack or chimney into the outdooratmosphere which exceed the above limit atany time. Maximum emission rate, based onTable 2 at N.J.A.C. 7:27-10.2(c) and thelocation of the facility (Essex County, Zone4) shall be demonstrated to the Departmentby stack test. Emission limit applies foreach MWC at all times, including startupand shutdown. [N.J.A.C. 7:27-10.2(c)]SO2: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs. Test shall demonstrate thatstandard is assured by continuous emissionmonitoring of SO2 in ppmvd. [FromRenewal BOP0800001.]. [N.J.A.C.7:27-22.16(a)]SO2: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(a)]27SO2 <= 1.2 lb/MMBTU gross heat inputdetermined as a 30-day rolling average. Noperson shall expand or reconstruct anexisting solid fuel-fired steam generatingunit or construct a new solid fuel-fired steamgenerating unit having a rated hourlycapacity that exceeds, or would exceed, as aresult of expansion, construction, and/orreconstruction, 250,000,000 British ThermalUnits (BTU) gross heat input unless thesulfur dioxide emissions, if the unit is aresource recovery facility, do not exceed theabove limit. This limit applies to eligibleresource recovery units. Emission limitapplies for each MWC at all times,including startup and shutdown. [N.J.A.C.7:27-10.3(a)3]None.None.None.Page 28 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement28Particulate Emissions <= 0.1 gr/dscf @ 12%CO2 (including ash, excluding thecontribution of auxiliary fuel). Emissionlimit applies for each MWC at all times,including startup and shutdown. [N.J.A.C.7:27-11.3(a)4]Particulate Emissions: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-11.3]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-11.3]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-11.3]29Opacity <= 1 Ringlemann Smoke Chart.Emission limit applies for each MWC at alltimes, including startup and shutdown.[N.J.A.C. 7:27-11.3(b)2ii]Opacity: Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. See most stringent opacitylimitation specified in this permit. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-11.3]Opacity: Recordkeeping by stack test resultsupon occurrence of event. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-11.3]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-11.3]30The provisions of 7:27-11.3(b)(2) shall notapply to: 1. Smoke emitted during thebuilding of a new fire, the shade orappearance of which is not greater thanNumber 2 of the Ringelmann smoke chartfor a period of three consecutive minutes;or ii. Emissions of such opacity within astack or chimney to a degree greater than theemission designated as Number 2 of theRingelmann smoke chart for a period notgreater than three consecutive minutes.[N.J.A.C. 7:27-11.3(b)3]None.None.None.31No person shall cause, suffer, allow orpermit the emission of particles of unburnedwaste or ash from any common incineratoror from any special incinerator which areindividually large enough to be visible whilesuspended in the atmosphere. Emissionlimit applies at all times, including startupand shutdown. [N.J.A.C. 7:27-11.3(c)]None.None.None.32Odor: No person shall construct, install, useor cause to be used any common incineratoror any special incinerator which will resultin odors being detectable by sense of smellin any area of human use or occupancy.Emission limit applies at all times, includingstartup and shutdown. [N.J.A.C.7:27-11.3(d)]None.None.None.Page 29 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement33Any person responsible for the use of anincinerator shall when ordered by theDepartment, provide the facilities andnecessary equipment for determining thedensity of smoke being discharged from astack or chimney and shall conduct suchsmoke tests using methods approved by theDepartment. Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27-11.3(e)1]None.Other: All smoke test data shall be recordedin a permanent log at such time intervals asspecified by the Department. Data shall bemaintained for a period of not less than oneyear and shall be available for review by theDepartment.[N.J.A.C. 7:27-11.3(e)1].None.34Any person responsible for the use of anexisting incinerator shall upon request of theDepartment provide such sampling facilitiesand testing facilities exclusive ofinstruments and sensing devices as may benecessary for the Department to determinethe nature and quantity of emissions fromsuch incinerators and shall during suchtesting operate the incinerator at a chargingrate of waste no less than the designedcapacity of the incinerator using materialsrepresentative of the types of wastesnormally burned. Emission limit applies atall times, including startup and shutdown.[N.J.A.C. 7:27-11.3(e)]None.None.None.35No person shall use or cause to be used anyincinerator unless all componentsconnected, or attached to, or serving theincinerator, including control apparatus arefunctioning properly and are in use, inaccordance with the permit to construct, andthe certificate to operate. Emission limitapplies at all times, including startup andshutdown. [N.J.A.C. 7:27-11.5(c)]None.None.None.36VOC (Total) <= 82.8 tons/yr based onPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.37NOx (Total) <= 1,248 tons/yr based onPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.38CO <= 1,656 tons/yr based onPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 30 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement39SO2 <= 996 tons/yr based onPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.40TSP <= 129 tons/yr based onPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.41PM-10 (Total) <= 299 tons/yr based onmodification BOP090001 (Total for threeMWCs). [N.J.A.C. 7:27-22.16(a)]None.None.None.42No person shall cause, suffer, allow, orpermit the emission of particles of unburnedwaste or ash which are individually largeenough to be visible while suspended in theatmosphere. [N.J.A.C. 7:27-22.16(e)]None.None.None.43HAPs (Total) <= 306 tons/yr fromPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.44Arsenic compounds <= 0.067 tons/yr fromPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.45Beryllium Compounds <= 0.003 tons/yrfrom Preconstruction Permits (Total forthree MWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.46Cadmium compounds <= 0.565 tons/yr fromPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.47Chromium compounds <= 0.158 tons/yrfrom Preconstruction Permits (Total forthree MWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.48HCl Emissions <= 284 tons/yr fromPreconstruction Permit (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.49Hydrogen fluoride <= 10.8 tons/yr fromPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.50Lead compounds <= 6.57 tons/yr fromPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 31 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement51Mercury compounds <= 0.14 tons / calendaryear (Total for three MWCs), or the facilityshall have demonstrated during the calendaryear that a minimum of 85% removal(revised by OP renewal BOP080001) ofmercury compounds had been achieved foreach quarterly average of all stack testsconducted foreach combustor required inthis Subject Item U1, OS0. This limit isbased on the concentration limit specified inthe Preconstruction Permit and in N.J.A.C.7:27-27.4(a). [N.J.A.C. 7:27-22.16(a)]Mercury compounds: Monitored bycalculations at the approved frequency usingthe following formula (using EPA F-Factor14,389 dscf @ 7% O2):Hg (tons per year) = X times 1 m3/35.3ft3 x 14389 dscf/MMBTU x 423 10E6Btu/hr/unit x 8760 hrs/yr x (1 gram/10E6ug) x (1 lb/454 grams) x 1 ton/2000 lb x 3(for 3 MWCs), where X equals the averageof all stack test results for the calendar yearexpressed in ug/dscm.The Department has adopted a morestringent mercury emission limit of 95%reduction, which will become a requirementon this facility January 3, 2012. [N.J.A.C.7:27-22.16(o)]Mercury compounds: Recordkeeping bymanual logging of parameter annually orquarterly (as appropriate.) Recordcalculations each quarter and/or annually,showing the running total foreach calendaryear. [N.J.A.C. 7:27-22.16(o)]None.52Nickel compounds <= 0.043 tons/yr fromPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.53Polycyclic organic matter <= 3.81 tons/yrfrom Preconstruction Permits (Total forthree MWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.54TCDD Emissions (2,3,7,8-) <= 0.000131tons/yr from Preconstruction Permits (Totalfor three MWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.55Ammonia <= 133 tons/yr based onPreconstruction Permits (Total for threeMWCs). [N.J.A.C. 7:27-22.16(e)]None.None.None.56Maximum Gross Heat Input <= 423MMBTU/hr (HHV) (each combustor) whilefiring municipal solid waste (MSW) and <=109 MMBTU/hr while firing No. 2 fuel oil.[N.J.A.C. 7:27-22.16(a)]Maximum Gross Heat Input: Monitored bycalculations once initially. Calculationscontained in letter dated October 30, 2001.[N.J.A.C. 7:27-22.16(e)]Other: Retain calculations in permanentfile.[N.J.A.C. 7:27-22.16(o)].None.57The permitted maximum steam productionrate for each boiler is247,500 pounds perhour at 650 psia and 752 degrees F(nominal). [N.J.A.C. 7:27-22.16(e)]Monitored by integrated steam flow monitorcontinuously , based on a 4 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]None.Page 32 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement58The emission limits specified in PSD permitand included herein at Subject Item U1, OSSummary, Refs #36-40 & 43-55 and at OS1,Refs #2-17 & #19-32 shall remain notapplicable during the start-up period.Clarification by modification BOP080002.[N.J.A.C. 7:27-22.16(a)]None.None.None.59Start-up Period: commences when theaffected incinerator begins the combustionof municipal waste, including continuous,semicontinuous, or batch feeding ofmunicipal solid waste to the furnace. Thestart-up period does not include anywarm-up period when the affected unit iscombusting only auxiliary fuel (fuel oil) andno municipal solid waste is beingcombusted. The duration of exemption fromemission limits during the start-up periodshall not exceed threehours. [N.J.A.C.7:27-22.16(e)]Start-up Period: Monitored by wastefeed/charge rate monitoring (solid)continuously. [N.J.A.C. 7:27-22.16(o)]Start-up Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]None.60To obtain start-up allowances, the facilitymust:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissionsduring start-up periods. [N.J.A.C.7:27-22.16(e)]None.None.None.61Start-up Period: Any visible emissionscaused by start-up shall not exceed anaverage of 10% opacity in any 6 minuteblock period. [N.J.A.C. 7:27-22.16(e)]Start-up Period: Monitored by continuousemission monitor continuously, based on 6minute blocks , using USEPA referencedMethod 9, or an equivalent methodapproved by USEPA and the Department.[N.J.A.C. 7:27-22.16(e)]Start-up Period: Recordkeeping by stripchart or data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]Submit a report: Upon occurrence of event.[N.J.A.C. 7:27-22.16(e)]Page 33 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement62The owner or operator shall develop aQA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)]Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis.[N.J.A.C. 7:27-22.16(o)].Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports.[N.J.A.C. 7:27-22.16(o)].Submit a report: Every April 30, July 30,October 30, and January 30 for thepreceding quarter year (the quarter yearsbegin on January 1, April 1, July 1, andOctober 1) electronically through theNJDEP online EEMPR web portal. Allquarterly and annual QA data shall beincluded in quarterly EEMPR reports andkept on file at the facility. The QA data mustbe made available to the Department uponrequest. [N.J.A.C. 7:27-22.16(o)]63Shutdown Period: commences when thefeeding of municipal solid waste to thehopper is terminated as a result of ascheduled shutdown or malfunction. Theshutdown period ends when municipal solidwaste is no longer combusting on the grate.The duration of exemption from emissionlimits during the shutdown period shall notexceed threehours. Malfunction resultingin shutdown of a unit shall be considered ashutdown, unless operation of the affectedunit is resumed before the shutdown iscomplete. Resuming the operation of a unitbefore shutdown is completed, if theshutdown is the result of malfunction, shallbe considered a malfunction. [N.J.A.C.7:27-22.16(e)]None.None.None.Page 34 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement64To obtain shutdown allowances, the facilitymust:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissionsduring shutdown periods. [N.J.A.C.7:27-22.16(e)]None.None.None.65Shutdown Period: Any visible emissionscaused by shutdown shall not exceed anaverage of 10% opacity in any 6 minuteblock period. [N.J.A.C. 7:27-22.16(e)]Shutdown Period: Monitored by continuousemission monitor continuously, based on 6minute blocks , using USEPA ReferencedMethod 9, or an equivalent methodapproved by USEPA and the Department.[N.J.A.C. 7:27-22.16(e)]Shutdown Period: Recordkeeping by stripchart or data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]Submit a report: As per the approvedschedule. [N.J.A.C. 7:27-22.16(e)]66The Permittee shall monitor incoming wastetrucks to determine whether they containlarge quantities of easily discernible yardwastes, such as grass clippings, leaves, treetrimmings, bushes and shrubs and preventbulk quantity of these wastes from beingcharged to the incinerators. {Attachment 1,Section J [N.J.A.C. 7:27-22.16(e)]None.None.None.67For each unit, continuous monitors andcontinuous recorders shall be installed,calibrated, tested and operated to measureand record opacity of the stack gas andemission concentrations of carbonmonoxide, oxygen, nitrogen oxides andsulfur dioxide before and after the acid gascontrol equipment. The Departmentreserves the right to require continuousmonitors and continuous recorders forammonia which may be imposed whencertifiable ammonia monitors becomeavailable. Monitors must comply with EPAperformance and siting specificationspursuant to 40 CFR Part 60, Appendix Band F. Equipment specifications, andcalibration and operating procedures mustbe submitted to the Department for approvalprior to installation. [N.J.A.C.7:27-22.16(e)]None.None.None.Page 35 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement68Each unit shall be equipped with continuousmonitors and continuous recorders whichshall be operated to accurately maintain thefollowing operating records:a. Removed by BOP080002b. scrubber slurry flow rate;c. secondary voltage, secondary currentand spark rate for each field of eachelectrostatic precipitator; andd. steam prodution rate/flow, steampressure and steam temperature of eachboiler.[From modification BOP080002.][N.J.A.C. 7:27-22.16(a)]None.None.None.69Operating Log: Permanently Bound Logbooks shall be kept foreach unit toaccurately maintain records. [N.J.A.C.7:27-22.16(e)]None.Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. For each unit, maintain thefollowing records:a. the specific times of operation of eachfurnace;b. the specific times of operation of theauxiliary burners;c. Removed by BOP080002;d. incidents of malfunctions (failures) ofelectrostatic precipitator, scrubber or SNCRsystem;e. Removed by BOP080002, andf. exceedances of emission standardsdetermined by continuous monitoring.[N.J.A.C. 7:27-22.16(a)]None.70MERCURY CONTROL SYSTEM:The permittee shall install and operatemercury emissions control apparatus(activated carbon injection system) designedto reduce at a minimum 80 percent of theemissions of mercury from each MSWincinerator. [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 36 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement71Mercury Emissions<=28 ug/dscm, based onan annual average and witheach test runcorrected to seven percent oxygen, as testedin accordance with a test protocol approvedpursuant to N.J.A.C. 7:27-27.8 (a) and (b)or:Mercury emissions at the exit of the controldevice of any unit shall not exceed 15percent (from N.J.A.C. 7:27-27.4(a)(2)(ii)after January 3, 2006) of the mercuryemissions in the effluent from the unit priorto the inlet to the control device based oneach quarterly average. [From modificationBOP090001.]The company must meet 28 ug/m3 or 85%control (from modification BOP080002),and also never exceed464 lbs per year. Ifthe company attains the 28 ug/m3 level, thenannual emissions would be less than 280lbs per year. [N.J.A.C. 7:27-27.4(a)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-27.4(c)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(o)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-27.8(a)]72The owner or operator of a MSW incineratorserved by a control apparatus shall performcompliance testing every quarter to measuremercury in the gas stream at the inlet of theair pollution control apparatus serving eachincinerator and simultaneously performcompliance testing every quarter to measuremercury in the gas stream at the exit of thecontrol device. There shall be at least a 45calendar day interval between the testingperformed for a given quarter and the testingperformed for the preceding quarter unlessotherwise approved by the Department.[N.J.A.C. 7:27-27.4(b)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-27.4(d)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-27.4(d)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-27.4(a)]Page 37 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement73Any person who achieves and maintainscompliance with the preceding mercurytesting requirements during two consecutiveyears may reduce the frequency of mercurytesting from each quarter to compliancetesting performed only once per year, notnecessarily in the first quarter of each year.Testing shall be not less than 9 months normore than 15 months after previous test testand at "worst case" conditions (See Ref #1.)Also facility shall conduct no less than 5tests during 5-year permit term. [Frommodification BOP080002.] However ifsubsequent testing fails to demonstratecompliance with the mercury testingrequirements, then the frequency of mercurytesting shall revert back to the quarterlyrequirement. [N.J.A.C. 7:27-22.16(a), (e)]& [N.J.A.C. 7:27-27.4(c)]Monitored by stack emission testingannually not less than 9 months nor morethan 15 months after previous test. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-27.4(c)]Recordkeeping by stack test resultsannually. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-27.9(c)]Submit a stack test report: As per theapproved schedule (by February 28 of thefollowing calendar year) to the Northernregional enforcement office and to theChief, Bureau of Technical Services. Reportof stack emission testing, including all testruns, shall be reviewed prior to submissionand certified by a licensed professionalengineer or an industrial hygienist certifiedby the American Board of IndustrialHygiene.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-27.9(c) &. [N.J.A.C.7:27-27.9(d)]74Mercury Emissions: The owner or operatorof any MSW incinerator that has a reagentbased mercury emision control system shalloperate each MSW incinerator at, or above,the optimized reagent feed rate establishedin the optimization tests and approved bythe Department. [N.J.A.C. 7:27-27.8(d)]None.None.None.75Any owner or operator of a MSWincinerator that submits to the Department areport of compliance testing, including alltest runs for a MSW incinerator shall havesuch report reviewed prior to submissionand certified by a registered professionalengineer or an industrial hygenist certifiedby the American Board of IndustrialHygiene. [N.J.A.C. 7:27-27.9(d)]None.None.None.76Any owner or operator of a MSWincinerator who submits to the Department areport of compliance testing, including alltest runs, shall certify that report. [N.J.A.C.7:27-27.9(f)]None.None.None.Page 38 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement77The owner or operator shall make anyrecord made pursuant to N.J.A.C. 7:27-27.9(e), i.e. the required mercury stack testrecords, available to the Department, or itsauthorized representatives, for inspection fora period of five years after the date therecord is made. [N.J.A.C. 7:27-27.9(g)]None.None.None.78The carbon injection system shall beoperated and maintained in accordance withthe facilitiy's Air Pollution ControlMaintenance Plan and the manufacturer'srecommendations. [N.J.A.C. 7:27-22.16(e)]None.None.None.79The Permittee shall, in accordance withN.J.A.C. 7:27-27.8(d), conduct optimizationtests on any single unit to determine theoptimized activated carbon feed rate formercury emission control. The resultantoptimum feed rate from the optimization testshall be applied to all three of the carboninjection units. The Permittee shall set theoptimum carbon feed rate at a level, abovewhich, there will be no appreciablereduction in mercury emissions relative tothe amount of activated carbon added. ThePermittee shall operate each carboninjection unit at, or above, the optimizedcarbon feed rate approved by theDepartment. The carbon injection mercurycontrol system shall be operated at all timeswhile solid waste is being combusted in theincinerator. [N.J.A.C. 7:27-22.16(a)]None.None.None.80The rate of carbon injection, from theoperating permit application, throughCD1010, 1011 & 1012 shall be greater thanor equal to 34 lb/hr in accordance with theapproval letter dated March 8, 2001.[N.J.A.C. 7:27-22.16(e)]Other: Carbon feed auger shall becontinuously monitored. In addition,Hopper Fill Cycle Rate shall be 2.0 hours orless and shall also be continuouslymonitored.[N.J.A.C. 7:27-22.16(e)].Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. All alarms indicatingproblems with auger operation and/or speed,or with Hopper Fill Cycle Rate shall berecorded. [N.J.A.C. 7:27-22.16(e)]None.Page 39 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement81The actual total quantity of carbon used atthe facility must equal or exceed theminimum required quarterly carbon usage(Qmin = R, carbon pounds per hour,multiplied by the total hours of waste feed toall three units during a calendar quarter.)[N.J.A.C. 7:27-22.16(e)]Monitored by material balance quarterly:once per quarter; quarters shall begin onJanuary 1, April 1, July 1, and October 1 ofeach year. Material balance shall be basedon bulk deliveries of carbon and storage siloinventories. As an alternative, hopper fills,which are recorded during each shift, maybe used to determine quarterly carbon usage.[From modification BOP080002.].[N.J.A.C. 7:27-22.16(a)]Recordkeeping by data acquisition system(DAS) / electronic data storage each monthduring operation , or manually in apermanently bound logbook to include thetotal hours of waste feed toeach unit, thetotal combined hours, total minimumcombined quantity of carbon required, andtotal combined amount of carbon actuallyused per quarter. Hopper fills also may berecorded. [N.J.A.C. 7:27-22.16(o)]Submit a report: Every quarter (threemonths) beginning on the first of the monthof the first full quarter following theeffective date of the approved permit.Quarters shall begin on January 1, April 1,July 1, and October 1 of each year with thequarterly excess emissions report within 30days of the end of each quarter. [N.J.A.C.7:27-22.16(o)]82The carbon feed auger speed foreachconsecutive three hour period (12 to 3, 3 to6, etc) must be maintained at or above thespeed that has been determined, by actualmeasurement during calibration, to deliverthe minimum required carbon feed rate. Ifthe auger or M-drive malfunctions wherecarbon is not being recorded by the DCS,hopper fills may be used to demonstratecompliance with continuous carbon feed.[From modification BOP080002.] [N.J.A.C.7:27-22.16(a)]None.None.None.83The operation below the minimumallowable carbon feed rate as indicated bythe auger speed is a permit violation unlesswithin three hours the condition that causesthe excursion is corrected, the proper rate isrestored, or the waste charging to the hopperof the affected furnace must cease untilcarbon feed is again at the minimumallowable rate. As an alternate, hopper fillsmay be used to demonstrate that theminimum allowable carbon feed is beingmaintained. [From modificationBOP080002.] The total time of all suchexcursions for each unit in a calendarquarter must not exceed 2% of the totaloperating time for the quarter. [N.J.A.C.7:27-22.16(a)]None.None.None.Page 40 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement84The carbon feed auger speed, versus actualcarbon delivery rate, shall be calibrated atleast once per quarter by actualmeasurements (collecting and weighing thecarbon delivered by the feeder) foreach unit.a. The maximum time betweencalibrations shall not be more than 120 days.b. The date and time of each calibrationand the results of the actual carbon deliveryrates must be recorded and must be madeavailable upon request by the Departmentpersonnel.c. Temporary diversions of carbon duringcalibrations of carbon feed auger speeds, orcalibrations of the carbon feed hoppers, forup to one (1) hour in any calendar day, donot apply to the preceding condition inaccordance with the approval letter datedNovember 18, 1998. [N.J.A.C.7:27-22.16(e)]Other: Conduct weigh-out test on carboninjection auger for one combustor every 120days.[N.J.A.C. 7:27-22.16(e)].Other: Retain records of carbon weigh-outprocedure. Upon occurence of event.[N.J.A.C. 7:27-22.16(e)].None.85During operation, the carbon injectionsystem operating parameter(s) that are theprimary indicator(s) of the carbon mass feedrate (e.g., screw feeder setting) must equalor exceed the level established duringperformance tests for mercury emissions.This is as required by 40 CFR 60.58b(m)(2).[40 CFR 60.39b(d)] & [40 CFR62.14109(b)]Other: Monitored by carbon feed rate, asrequired at 40 CFR 60.58b(m)(2). [40 CFR60.39b(d)]&[40 CFR 62.14109(b)].Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslyThe facility shall record the average carbonmass feed rate (in kg/hr or lb/hr) estimatedfor eachhour of operation. This is asrequired at 40 CFR 60.59b(d)(4)(iii). Also,as required at 40 CFR 60.59b(d)(15), thefacility shall record the dates where thecarbon feed rate is less than the levelsestablished by the performance tests formercury and dioxins/furans. [40 CFR60.39b(d)] &. [40 CFR 62.14109(a)]None.86ACID GAS SCRUBBER:Each scrubber shall be operated andmaintained in accordance with the facility'sAir Pollution Control Maintenance Plan andthe manufacturer's recommendations.[N.J.A.C. 7:27-22.16(e)]None.None.None.87Lime slurry shall be used as scrubbingchemical additive. [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 41 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement88SO2 Removal Efficiency: Each scrubbershall be capable of reducing the averageSO2 concentration in the stack gas to <= 94ppmdv @ 7% O2 or to <= 30% of the SO2concentration (ppmdv @ 7% O2) at the inletof the scrubber. [N.J.A.C. 7:27-22.16(e)]SO2 Removal Efficiency: Monitored bycontinuous emission monitor continuously,based on a 1 hour block average , beginningand ending on the hour. [N.J.A.C.7:27-22.16(e)]SO2 Removal Efficiency: Recordkeeping bystrip chart or data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]None.89Hydrogen chloride: Each scrubber shall becapable of reducing the average HClconcentration in the stack gas to <= 47ppmdv @ 7% O2 or to <= 10% of the HClconcentration (ppmdv @ 7% O2) at the inletof the scrubber. [N.J.A.C. 7:27-22.16(e)]Hydrogen chloride: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(e)]Hydrogen chloride: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]90ELECTROSTATIC PRECIPITATOR:The electrostatic precipitator shall beoperated and maintained in accordance withthe facility's Air Pollution ControlMaintenance Plan and the manufacturer'srecommendations. [N.J.A.C. 7:27-22.16(e)]None.None.None.91The permittee shall continuously monitorand record the secondary voltage, secondarycurrent and spark rate for each field of eachESP. [N.J.A.C. 7:27-22.16(e)]Monitored by continuous emission monitorcontinuously. [N.J.A.C. 7:27-22.16(e)]Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]None.Page 42 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement92The temperature at the particulate controldevice inlet shall not exceed the maximumdemonstrated particulate matter controldevice temperature as defined in 40 CFR60.51b by more than 17 degrees Celsius (or31 degrees Fahrenheit), except: (1) Duringthe annual dioxin/furan performance test the2 weeks preceding the annual dioxin/furanperformance test, no particulate mattercontrol device temperature limitations areapplicable; (2) The particulate matter controldevice temperature limits may be waived inaccordance with permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluationsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of the-art for controlling facilityemissions. This is based on the requirementat 40 CFR 60.53b(c). [40 CFR 60.39b(d)]& [40 CFR 62.14104(b)]Monitored by temperature instrumentcontinuously, based on a 1 hour blockaverage which shall be used to calculate4-hour block arthithmetic avarages, basedon the requirement at 40 CFR 60.58b(i)(7).[40 CFR 60.39b(d)] &. [40 CFR62.14109(b)]Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. All 4-hour block arithmetictemperature averages shall be computed andrecorded and be available for submittal tothe Administrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(ii). [40 CFR 60.39b(d)] &.[40 CFR 62.14109(a)]None.93THERMAL DeNOx SYSTEM:The SNCR shall be operated and maintainedin accordance with the facility's AirPollution Control Maintenance Plan and themanufacturer's recommendations. [N.J.A.C.7:27-22.16(e)]None.None.None.94See GR1 for applicable requirements fromNSPS Subpart A, General Provisions. [40CFR 60]None.None.None.95The facility is not subject to the nitrogenoxide standards in the NSPS for industrialboilers (40 CFR, Part 60, Subpart Db)unless more than 2.2 million gallons of oil isburned in any consecutive 365-day period.[40 CFR 60.44b(e)]Monitored by review of fuel deliveryrecords each month during operation, basedon a consecutive 12 month period (rolling 1month basis). [N.J.A.C. 7:27-22.16(a)]Recordkeeping by invoices / bills of ladingeach month during operation. [N.J.A.C.7:27-22.16(a)]None.Page 43 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement96The standards under 40 CFR 62, SubpartFFF apply at all times except during periodsof startup, shutdown, or malfunction.Duration of startup, shutdown, ormalfunction periods are limited to 3 hoursper occurrence. The startup periodcommences when the affected facility beginsthe continuous burning of municipal solidwaste and does not include any warmupperiod when the affected facility iscombusting fossil fuel or othernonmunicipal solid waste fuel, and nomunicipal solid waste is being fed to thecombustor. Continuous burning is thecontinuous, semicontinuous, or batchfeeding of municipal solid waste forpurposes of waste disposal, energyproduction, or providing heat to thecombustion system in preparation for wastedisposal or energy production. The use ofmunicipal solid waste solely to providethermal protection of the grate or hearthduring the startup period when municipalsolid waste is not being fed to the grate isnot considered to be continuous burning.This is based on the requirement at 40 CFR60.58b(a)(1). 40 CFR 60.39b(d) & [40 CFR62.14109(b)]None.None.None.97Opacity <= 10 % (6-minute average),emission limit for opacity exhibited by thegases discharged to the atmosphere from adesignated facility except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR60.33b(a)(1)(iii)] &. [40 CFR62.14103(a)(1)]Opacity: Monitored by continuous opacitymonitoring system continuously, based on 6minute blocks. The continuous opacitymonitoring system shall conform toPerormance Specification 1 in 40 CFR 60,appendix B. This is as required at 40 CFR60.58b(c)(8). See stack testing requirementsin U1 OS0. 40 CFR 60.58b(c)(11). [40CFR 62.14109(b)]Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. All 6-minute opacity levelsshall be available for submittal or reviewonsite by an inspector, as required at 40CFR 60.59b(d)(i)(A). . See stack testingrequirements in U1 OS0. Recordkeeping forstack testing is as required at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.Page 44 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement98Particulate Emissions <= 25 mg/dscm @ 7%O2 from each MWC on and after April 28,2009, except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b). [40 CFR60.33b(a)(1)(i)] &. [40 CFR62.14103(a)(1)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the requirements at40 CFR 60.58b(c)(9). [40 CFR62.14109(b)]Particulate Emissions: Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.99Nitrogen oxides (NOx) <= 205 ppmvd @7% O2 , 24-hour daily arithmetic average(midnight to midnight) from each MWCexcept during periods of startup, shutdown,and malfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). 40 CFR 60.33b(d) &.[40 CFR 62.14103(d)]Nitrogen oxides (NOx): Monitored bycontinuous emission monitoring systemcontinuously, based on a 1 hour blockaverage. Monitor as specified at 40 CFR60.58b(h)(5). EPA Reference Method 19,section 4.1, shall be used for determiningthe 24-hour daily arithmetic averagenitrogen oxides emission concentration. [40CFR 62.14109(b)]Nitrogen oxides (NOx): Recordkeeping bystrip chart or data acquisition (DAS) systemcontinuously. All 1-hour average nitrogenoxide concentrations shall be recorded andbe available for submittal or review onsiteby an inspector. This is as specified at 40CFR 60.59b(d)(2)(i)(C). [40 CFR62.15109(a)]None.100Lead Emissions <= 0.4 mg/dscm @ 7% O2from each MWC on and after April 28,2009, except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b). 40 CFR60.33b(a)(4) &. [40 CFR 62.14103(a)(2)]Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the Method 29requirements at 40 CFR 60.58b(d)(1). [40CFR 62.14109(b)]Lead Emissions: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.101Cadmium Emissions <= 0.035 mg/dscm @7% O2 from each MWC on and after April28, 2009 except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b). [40 CFR60.33b(a)(2)(i) &. [40 CFR 62.14103(a)(2)]Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring requirements are based on therequirements at 40 CFR 60.58b(d)(1). [40CFR 62.14109(b)]Cadmium Emissions: Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.102Mercury Emissions <= 0.05 mg/dscm @ 7%O2 or 15 percent of the potential mercuryemission concentration (85-percentreduction by weight), corrected to 7%oxygen, whichever is less stringent, fromeach MWC on and after April 28,2009except during periods of startup, shutdown,and malfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). [40 CFR 60.33b(a)(3)]&. [40 CFR 62.14103(a)(3)]Mercury Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the requirements of40 CFR 60.58b(d)(2). [40 CFR62.14109(b)]Mercury Emissions: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0.. Recordkeeping isbased on the requirements at 40 CFR50.59b(d)(9)(i). [40 CFR 62.14109(a)]None.Page 45 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement103SO2 <= 29 ppmvd @ 7% O2 , or 25% of thepotential sulfur dioxide emissionconcentration (75 percent reduction byweight or volume) whichever is lessstringent, from each MWC except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). Compliance with thisemission limit is based on a 24-hour dailygeometric mean. [40 CFR 60.33b(b)(3)(i)]&. [40 CFR 62.14103(b)(1)]SO2: Monitored by continuous emissionmonitoring system continuously, based on adaily average (a 24-hour daily geometricaverage), or a daily geometric averagepercent reduction using EPA ReferenceMethod 19. This is based on the requirementat 40 CFR 60.58b(e)(4). [40 CFR62.14109(b)]SO2: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.The owner or operator shall maintainrecords of all 1-hour average sulfur dioxideemission concentrations. This is as specifiedat 40 CFR 60.59b(d)(2)(i)(B). [40 CFR61.14109(a)]None.104HCl Emissions <= 29 ppmvd @ 7% O2 or5% of the potential hydrogen chlorideemission concentration (95 percentreduction by weight or volume) whichever isless stringent, from each MWC exceptduring periods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). [40 CFR60.33b(b)(3)(i)] &. [40 CFR62.14103(b)(2)]HCl Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring, including detemining %reduction, is based on the requirements at 40CFR 60.58b(f). [40 CFR 62.14109(b)]HCl Emissions: Recordkeeping by stack testresults annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.105Dioxins/Furans (Total) <= 35 ng/dscm @7% O2. On and after April 28, 2009, theemission limit for designated facilities thatemploy an electrostatic precipitator-basedemission control system is 35 nanograms perdry standard cubic meter (total mass),corrected to 7 percent oxygen. [40 CFR60.33b(c)(1)(ii)]Dioxins/Furans (Total): Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is as required at 40 CFR60.58b(h)(5), except as specified at 40 CFR62.14109(d)(1). [40 CFR 62.14109(b)] &.[40 CFR 62.14109(d)(1)]Dioxins/Furans (Total): Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. This is asspecified at 40 CFR 60.59b(d)(9)(i). [40CFR 62.14109(a)]None.106CO <= 100 ppmvd @ 7% O2 fromeachMWC except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b), 40 CFR60.34b(a) and 40 CFR 60.58b(a)(1). [40CFR 62.14104(a)]CO: Monitored by continuous emissionmonitoring system continuously, based on a1 hour block average which shall be used tocalcuate a 4-hour block average. Thecontinuous emission monitoring systemshall be operated according to PerformanceSpecification 4A in 40 CFR 60, appendix B.Monitoring is as specified at 40 CFR60.58b(i)(1), 40 CFR 60.58b(i)(3), and 40CFR 60.58b(i)(4). [40 CFR 62.14109(b)]CO: Recordkeeping by strip chart or dataacquisition (DAS) system continuously. All1-hour average CO concentrations shall berecorded and available for submittal to theadministrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(i)(D). [40 CFR62.14109(a)(1)]None.Page 46 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement107No owner or operator of an affected facilityshall cause it to operate at a load levelgreater than 110 percent of the maximumdemonstrated municipal waste combustorunit load as defined in 40 CFR 60.51b,except: (1) During he annual dioxin/furanperformance test and the 2 weeks precedingthat test, no municipal waste combustor unitload limit is applicable; (2)The municipalwaste combustor unit load limit may bewaived in accordance with permissiongranted by the Administrator or delegatedState regulatory authority for the purpose ofevaluating system performance, testing newtechnology or control technologies,diagnostic testing, or related activities forthe purpose of improving facilityperformance or advancing the state-of-theart for controlling facility emissions. This isas stated at 40 CFR 60.53b(b). [40 CFR60.39b(d)]& [40 CFR 62.14104(b)]Other: The owner or operator shall operate asteam or feedwater flow meter on acontinuous basis, as required at 40 CFR60.58(i)(6)(i). Steam (or feed water flow)flow calculations as required under 40 CFR60.58(i)(6)(i) shall be in accordance withASME PTC 4.1-1964 (Reaffirmed 1991),Power test codes : Test Code for SteamGenerating Units (with 1968 and 1969Addenda). For design, construction,installation, calibration, and use of nozzlesand orifices required in 40 CFR60.58(i)(6)(ii), proceed in accordance withthe recommendations in ASME InterimSupplement 19.5 on Instruments andApparatus: Application, Part II of FluidMeters, 6th Edition (1971). Measurementdevices such as flow nozzles and orifices arenot required to be recalibrated after they areinstalled, as stipulated at 40 CFR58b(i)(6)(iii). Also, as stipulated at 40 CFR58b(i)(6)(iv), all signal conversion elementsassociated with steam (or feedwater flow)measurements must be calibrated accordingto the manufacturer's instructions beforeeach dioxin/furan performance test, and atleast once per year. [40 CFR 60.39b(d)]&[40 CFR 62.14104(b)].Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslybased on the requirment at 40 CFR60.58(i)(6)(i). [40 CFR 60.39b(d)] &. [40CFR 62.14104(b)]None.Page 47 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement108Each chief facility operator and shiftsupervisor must obtain and maintain acurrent provisional operator certificationfrom either the American Society ofMechanical Engineers (QRO-1-1994) or aState certification program. [40 CFR60.35b, 40 CFR 60.39b(d), 40 CFR 60.54b]& [40 CFR 62.14105(a)]None.Other: The facility shall maintain thefollowing records for a period of five years:Records showing the names of the municipalwaste combustor chief facility operator, shiftsupervisors and control room operators whohave been fully certified or who areprovisionally certified by the AmericanSociety of Mechanical Engineers (ASME)or an equivalent State approved certificationprogram, including the dates of initial andrenewal and renewal certifications anddocumentation of current certification.Records showing the names of the municipalwaste combustor chief facility operator, shiftsupervisors and control room operators whohave completed the EPA municipal wastecombustor operator training course or aState approved equivalent course includingdocumentation of training completion.This is based on the recordkeepingrequirements at 40 CFR 60.59b(d)(12)[40 CFR 62.14105(a)].None.109Each chief facility operator and shiftsupervisor must complete full certificationor must have scheduled a full certificationexam with either the American Society ofMechanical Engineers (QRO-1-1994) or aState certification program. 40 CFR60.39b(d)& [40 CFR 62.14105(b)]None.None.None.Page 48 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement110The facility must not be operated unless oneof the following persons is on duty:- a fully certified chief facility operator;- a provisionally certified chief facilityoperator who is scheduled to take the fullcertification exam no later than 12 monthsafter the effective date of 40 CFR 62Subpart FFF;- a fully certified shift supervisor; or- a provisionallycertified shift supervisorwho is scheduled to take the fullcertification exam no later than 12 monthsafter the effective date of 40 CFR 62Subpart FFF.If one of the persons listed above mustleave the facility during their operating shift,a provisionally certified control roomoperator who is onsite may fulfill thisrequirement. [40 CFR 60.39b(d), 40 CFR60.54b(i)] & [40 CFR 62.14105(c)]None.None.None.111As further clarification to the preceding"Stand-in" Provisions, a provisionallycertified control room operator can stand-infor a certified plant or shift supervisor whenthey are off site for periods of up to eighthours without notification of EPA, forperiods up to two weeks if EPA is notifiedin writing, and case by case withenforcement discretion for periods longerthan two weeks if EPA is notified in writingwith adequate detail of the reasons for thesituation and if the MWC ownerdemonstrates to EPA that a good faith effortis being made to correct the problem.[N.J.A.C. 7:27-22.16(a)]None.None.None.Page 49 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement112Each chief facility operator, shift supervisorand control room operator at an affectedfacility must complete the EPA municipalwaste combustor operator training course orthe State municipal waste operator trainingcourse, except for chief facility operators,shift supervisors, and control room operatorswho have obtained full certification from theASME on or before the effective date of 40CFR 62 Subpart FFF. [40 CFR 60.39b(d),40 CFR 60.54b] &. [40 CFR 62.14105(d)]None.None.None.113OPERATING MANUAL:The facility must develop and update on ayearly basis a manual that must, at aminimum, address the following elements ofmunicipal waste combustor unit operation:- A summary of the applicable standardsof 40 CFR 62 Subpart FFF;- A description of basic combustiontheory applicable to a MWC unit;- Procedures for receiving, handling andfeeding MSW;- Procedures for MWC unit startup,shutdown and malfunction;- Procedures for maintaining propercombustion air supply levels;- Procedures for operating the MWC unitwithin the standards established under 40CFR 62 Subpart FFF;- Procedures for responding to periodicupset or off-specification conditions;- Procedures for minimizing particulatematter carryover;- Procedures for handling ash;- Procedures for monitoring MWC unitemissions;- Reporting and Recordkeepingprocedures. [40 CFR 60.39b(d), 40 CFR60.54b(e)] & [40 CFR 62.14105(e)]None.Other: The operating manual and records oftraining must be available for inspection byUSEPA or the Department upon request.[40 CFR 60.39b(d)] &[40 CFR62.14105(g)].None.Page 50 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement114TRAINING FOR OPERATING MANUALREVIEW:- The facility must establish a trainingprogram to review the operating manualaccording to the schedule specified belowwith each person who has responsibilitiesaffecting the operation of the facility,including but not limited to, chief facilityoperators, shift supervisors, control roomoperators, ash handlers, maintenancepersonnel and crane/load handlers.Each person undergoing the manual reviewtraining shall do so no later than the datesspecified below, whichever is later:- The date prior to the day the personassumes responsibilities affecting MWC unitoperation; or- The date 12 months after the effectivedate of 40 CFR 62 Subpart FFF; or- Annually following the initial review.ACCESS TO OPERATING MANUAL:The operating manual must be kept in alocation readily accessible to each personrequired to undergo training. [40 CFR60.39b(d), 40 CFR 60.54b(f) & (g)] & [40CFR 62.14105(f)]None.Other: The facility shall maintain recordsshowing the names of persons who havecompleted a review of the operating manualincluding the date of initial review andsubsequent annual reviews. This is based onthe recordkeeping requirement at 40 CFR50.59b(d)(13). [40 CFR 60.39b(d)] &[40CFR 62.14105(a)].None.Page 51 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement115SEMI-ANNUAL REPORT:The facility shall submit a semi-annualreport which shall include the following:- Information recorded which indicates theaverage sulfur dioxide, nitrogen oxides,carbon monoxide, municipal wastecombustor unit load level, particulate mattercontrol device inlet temperature or opacitydata were above the applicable limits withreasons for such exceedances and adescription of the corrective action taken.- A copy of the annual test reportdocumenting the emissions level and thecorrective action taken if the test reportindicates any particulate matter, opacity,cadmium, lead, mercury, dioxins/furans,hydrogen chloride or fugitive ash emissionlevels that were above applicable pollutantlimits.- Identification of the calendar dates whenthe average hourly carbon feed rate wasbelow the required feed rate with reasons forsuch occurrences and a description ofcorrective action taken.- Identification of the calendar dates whenthe average hourly carbon feed rate is notoperational, with reasons for suchoccurrences and a description of correctiveaction taken. This is as stated at 40 CFR60.59b(h). [40 CFR 60.39b(d)] & [40 CFR62.14109(a)]None.Other: All semi-annual reports must bemaintained on site as a paper copy for aminimum of 5 years. This is as stated at 40CFR 60.59b(j). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].Submit a report: As per the approvedschedule that follows to EPA Region II andthe appropriate Regional EnforcementOffice of NJDEP. The report for the firsthalf of the calendar year must be submittedby August 1 of the same year. The reportfor the second half of the calendar year mustbe submitted by February 1 of the followingyear. This is as stated at 40 CFR 50.59(h).[40 CFR 60.39b(d)] &. [40 CFR62.14109(a)]Page 52 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement116SEMI-ANNUAL REPORT (continued):Upon issuance of the operating permit, thesemi-annual report shall include thefollowing:- A list of the particulate matter, opacity,cadmium, lead, mercury, dioxins/furans,hydrogen chloride and fugitive ash emissionlevels achieved during performance tests- A list of the highest emission levelrecorded for sulfur dioxide, nitrogendioxides, carbon monoxide, municipal wastecombustor load level and particulate mattercontrol device inlet temperature.- A list of the highest opacity level measured- The total number of days that the minimumnumber of hours of data for sulfur dioxide,nitrogen oxides, carbon monoxide,municipal waste combustor unit load leveland particulate matter control device inlettemperature were not obtained for thecalculation of the average emissionsconcentrations or parameters.- The total number of hours that data forsulfur dioxide, nitrogen oxides, carbonmonoxide, municipal waste combustor unitload and particulate matter control deviceinlet temperature were excluded from thecalculation of average emissionsconcentrations or parameters. This is basedon the requirements of 40 CFR 59b(g)(1).[40 CFR 60.39b(d)] & [40 CFR62.14109(a)]None.Other: All semi-annual reports must bemaintained on site as a paper copy for aminimum of 5 years. This is as stated at 40CFR 60.59b(j). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].Submit a report: As per the approvedschedule that follows to EPA Region II andthe appropriate Regional EnforcementOffice of NJDEP. The report for the firsthalf of the calendar year must be submittedby August 1 of the same year. The reportfor the second half of the calendar year mustbe submitted by February 1 of the followingyear. This is based on the requirments at 40CFR 60.59b(g). [40 CFR 60.39b(d)] &. [40CFR 62.14109(a)]Page 53 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement117SEMI-ANNUAL REPORT (continued):-The facility shall also provide a summaryreport with the same data specified in thesemi-annual reports for the preceding year inorder to provide the Administrator with asummary of the performance of the facilityover a 2 year period. This summary reportshall highlight any emission or parameterlevel that did not achieve the requiredemission or parameter limits.- The facility will also include a notificationof intent to begin reduced dioxin/furanperformance testing schedule as allowed in40 CFR 60.58(g)(5)(iii), i.e. NSPS SubpartEb. These are based on the requirements of40 CFR 60.59b(g). [40 CFR 60.39b(d)] &[40 CFR 62.14109(a)]None.Other: All semi-annual reports must bemaintained on site as a paper copy for aminimum of 5 years. This is as stated at 40CFR 60.59b(j). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].Submit a report: As per the approvedschedule that follows to EPA Region II andthe appropriate Regional EnforcementOffice of NJDEP. The report for the firsthalf of the calendar year must be submittedby August 1 of the same year. The reportfor the second half of the calendar year mustbe submitted by February 1 of the followingyear. This is based on the requrements at 40CFR 60.59b(g). [40 CFR 60.39b(d)] &.[40 CFR 62.14109(a)]118REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of the calendar dates when anyof the average emission concentrations,percent reductions, operating parameters oropacity levels are above applicable limits,with reasons for such exceedances and adescription of corrective action taken. Thisis as stated at 40 CFR 60.59b(d)(3). [40CFR 60.39b(d)]& [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109].None.119REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of the calendar dates forwhich the minimum number of hours of thedata specified below have not been obtainedand the reasons for not obtaining sufficientdata and a description of the correctiveaction taken:- Sulfur Dioxide emissions data- Nitrogen Oxides emissions data- Carbon Monoxide emissions data- Municipal waste combustor unit load data- Particulate matter control devicetemperature dataThis is as stated at 40 CFR 60.59b(d)(6). [40CFR 60.39b(d)] & [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.Page 54 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement120REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of each occurrence that sulfurdioxide emissions data, nitrogen oxidesemissions data or operational data (i.e.carbon monoxide emissions, unit load andparticulate matter control devicetemperature) have been excluded from thecalculation of average emissionconcentration or parameters, and the reasonsfor excluding the data. This is as stated at40 CFR 60.59b(d)(7). [40 CFR 60.39b(d)]& [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.121REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:The results of daily drift test and quarterlyaccuracy determinations for sulfur dioxide,nitrogen oxides and carbon monoxidecontinuous emission monitoring systems asrequired under 40 CFR Part 60 Appendix F,Procedure 1. This is based on therequirements at 40 CFR 60.59b(d)(8). [40CFR 60.39b(d)] & [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.Page 55 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement122REPORTING/RECORDKEEPING OFANNUAL PERFORMANCE TESTS:The facility shall maintain the followingrecords for a period of at least five years:The test reports documenting the results ofall annual performance tests shall berecorded along with supporting calculationsspecifically as follows:- The results of all annual performance testsconducted to determine compliance withparticulate matter, opacity, cadmium, lead,dioxin/furans, hydrogen chloride andfugitive ash emission limits.- The maximum demonstrated municipalwaste combustor unit load and maximumdemonstrated particulate matter controldevice temperature during dioxin/furanperformance tests.This condition is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(d)] & [40 CFR 62.14109(a)]None.Other: Maintain records for a period of atleast 5 years from the date of record. [40CFR 60.39b(d)] &[40 CFR 62.14109(a)].None.Page 56 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U1 Municipal Waste Combustors (E1, E2 & E3) - Subject to NSPS Subparts Cb and 40 CFR 62 Subpart FFFOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Unless otherwise specified, the emissionlimits specified under this operating scenarioshall apply at all times, except for start-upand shutdown periods. [N.J.A.C.7:27-22.16(e)]None.None.None.2Maximum emission rate of Non-MethaneHydrocarbons as Methane, VOC (Total) <=6.3 lb/hr. [N.J.A.C. 7:27-22.16(e)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]3Maximum concentration of Non-MethaneHydrocarbons as Methane, VOC (Total) <=66 ppmvd @ 7% O2. [N.J.A.C.7:27-22.16(e)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]4NOx (Total) <= 95 lb/hr frompreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Monitored by stack emissiontesting every 5 years, based on the averageof three 1-hour tests. Three test runs mustbe conducted oneach unit, with ammoniainjection, to determine compliance.[N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by stack testresults every 5 years. [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]5NOx (Total) <= 300 ppmvd @ 7% O2. Theemission limitation shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitor continuously, based on a 1hour block average , beginning and endingon the hour. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by strip chartor data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]None.6NOx (Total) <= 155 ppmvd @ 7% O2. Theemission limitation shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitor continuously, based on a24 hour period block, beginning and endingat midnight. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by strip chartor data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]None.OS1 Operation of MWC #1 at Maximum Input (423 MMBtu/hr), OS3 Operation ofMWC # 2 at Maximum Input (423 MMBtu/hr),OS5 Operation of MWC # 3 at Maximum Input (423 MMBtu/hr)Page 57 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7CO <= 126 lb/hr from preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]CO: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]CO: Recordkeeping by stack test resultsupon occurrence of event. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]8CO <= 400 ppmvd @ 7% O2. The emissionlimitation shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]CO: Monitored by continuous emissionmonitor continuously, based on a 1 hourblock average , beginning and ending on thehour. [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. See most stringent limitationspecified in this permit. [N.J.A.C.7:27-22.16(e)]9CO <= 100 ppmvd @ 7% O2. The emissionlimitation shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]CO: Monitored by continuous emissionmonitor continuously, based on a 96 hourrolling average based on a 1 hour blockaverage beginning and ending on the hour.[N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. See most stringent limitationspecified in this permit. [N.J.A.C.7:27-22.16(e)]10The CO and NOx emission limits specifiedin permit condition, for normal steady stateoperation shall not apply during periods,including warm-up periods, when no wasteis burned and fossil fuel is being combusted.Only auxiliary fuel (fuel oil) shall becombusted during warm-up periods, and nomunicipal solid waste shall combusted. Thewarm-up period begins upon initiation ofauxiliary fuel (fuel oil) combustion in thefurnace. The duration of exemption fromemission limits during these periods shallnot exceed 10 consecutivehours perwarm-up period. [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 58 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement11SO2 <= 75.8 lb/hr. [N.J.A.C. 7:27-22.16(e)]SO2: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs [From BOP080001.]. [N.J.A.C.7:27-22.16(o)]SO2: Recordkeeping by stack test resultsupon occurrence of event [FromBOP080001.]. [N.J.A.C. 7:27-22.16(o)]None.12SO2 <= 94 ppmvd @ 7% O2. This limitshall not apply for 1-hour block periodsduring which the average concentration ofSO2 (ppmdv@7%O2) in the stack gas isless than 30% of the average concentrationof SO2 (ppmdv@7%O2) at the inlet to theacid gas control equipment. [N.J.A.C.7:27-22.16(e)]SO2: Monitored by continuous emissionmonitor continuously, based on a 1 hourblock average , beginning and ending on thehour. [N.J.A.C. 7:27-22.16(e)]SO2: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]None.13SO3 and H2SO4, as converted andexpressed as H2SO4 <= 4 lb/hr. [N.J.A.C.7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]14Particulate Emissions <= 9.8 lb/hr frompreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]15Particulate Emissions <= 0.014 gr/dscf @7% O2. [N.J.A.C. 7:27-22.16(e)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]16Particulate Emissions <= 0.028 gr/dscf @7% O2 for each individual test run,including test runs during which sootblowing is performed. [N.J.A.C.7:27-22.16(e)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]17PM-10 (Total) <= 22.8 lb/hr Hourlyemission rate established from stack test(s)results. [Modification BOP090001].[N.J.A.C. 7:27-22.16(a)]PM-10 (Total): Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]PM-10 (Total): Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Page 59 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement18Any visible emissions shall not exceed anaverage Opacity <= 10 %. [N.J.A.C.7:27-22.16(e)]Opacity: Monitored by continuous emissionmonitor continuously, based on 6 minuteblocks. The discrete block average willbegin on the hour. [N.J.A.C. 7:27-22.16(e)]Opacity: Recordkeeping by strip chart ordata acquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Notify by phone: Upon occurrence of event.Any non-compliance shall be reported.[N.J.A.C. 7:27-22.16(e)]19Arsenic compounds <= 0.0051 lb/hr.[N.J.A.C. 7:27-22.16(e)]Arsenic compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Arsenic compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]20Beryllium Compounds <= 0.00025 lb/hr.[N.J.A.C. 7:27-22.16(e)]Beryllium compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Beryllium compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]21Cadmium compounds <= 0.043 lb/hr.[N.J.A.C. 7:27-22.16(e)]Cadmium compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Cadmium compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]22Chromium compounds <= 0.012 lb/hr.[N.J.A.C. 7:27-22.16(e)]Chromium compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Chromium compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]23HCl Emissions <= 21.6 lb/hr. [N.J.A.C.7:27-22.16(e)]HCl Emissions: Monitored by stackemission testing annually, based oneach ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]HCl Emissions: Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]24HCl Emissions <= 47 ppmvd @ 7% O2.This limit shall not apply for 1-hour blockperiods during which the averageconcentration of HCl (ppmdv @ 7% O2) inthe stack gas is less than 10% of the averageconcentration of HCl (ppmdv @ 7% O2) atthe inlet to the acid gas control equipment.[N.J.A.C. 7:27-22.16(e)]HCl Emissions: Monitored by stackemission testing annually, based oneach ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]HCl Emissions: Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 60 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement25Hydrogen fluoride <= 0.82 lb/hr. [N.J.A.C.7:27-22.16(e)]Hydrogen fluoride: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Hydrogen fluoride: Recordkeeping by stacktest results upon occurrence of event. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]26Lead compounds <= 0.5 lb/hr. [N.J.A.C.7:27-22.16(e)]Lead compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Lead compounds: Recordkeeping by stacktest results upon occurrence of event. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]27Mercury compounds <= 0.053 lb/hr inaccordance with the July 27,1997preconstruction permit and confirming letterdated August 27, 2002. [N.J.A.C.7:27-22.16(e)]Mercury compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Mercury compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]28Nickel compounds <= 0.0033 lb/hr.[N.J.A.C. 7:27-22.16(e)]Nickel compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Nickel compounds: Recordkeeping by stacktest results upon occurrence of event. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]29TCDD Emissions (2,3,7,8-) <= 0.00001lb/hr. [N.J.A.C. 7:27-22.16(e)]TCDD Emissions (2,3,7,8-): Monitored bystack emission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]TCDD Emissions (2,3,7,8-): Recordkeepingby stack test results upon occurrence ofevent. See stack testing requirements in U1OS0. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]30Polycyclic aromatic hydrocarbons, orPolycyclic organic matter <= 0.29 lb/hr.[N.J.A.C. 7:27-22.16(a)]Polycyclic organic matter: Monitored bystack emission testing prior to permitrenewal, based on the average of threeDepartment validated stack test runs. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Polycyclic organic matter: Recordkeepingby stack test results upon occurrence ofevent. See stack testing requirements in U1OS0. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]31Emissions of benzo(a) pyrene, carbontetrachloride, formaldehyde,perchloroethylene (tetrachloroethylene),trichloroethylene and vinyl chloride shall bebelow the reporting threshold of N.J.A.C.7:27-22, Tables A & B and must bemeasured using methods approved by DEP.[N.J.A.C. 7:27-22.16(e)]Monitored by stack emission testing prior topermit renewal, based on the average ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Recordkeeping by stack test results uponoccurrence of event. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 61 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement32Ammonia <= 10.1 lb/hr. [N.J.A.C.7:27-22.16(e)]Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns. See stack testing requirements in U1OS0. [N.J.A.C. 7:27-22.16(o)]Ammonia: Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]33The acid gas control device CD1001 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Absorber fluid medium: Lime solutionPump Disch Press: 0 - 300 Ft H2OMax. solution flow rate: 30 gpmFlow monitor: Bailey Net 90 Control SystemGas flow rate: 215-315,000 acfmAbsorber inlet/outlet pressure: 5.5 & 6inches w.c.Gas temperature: 302 - 491 deg FDesign efficiency: 70% [N.J.A.C.7:27-22.16(a)]None.None.None.34Operating Control Efficiency >= 70 %control. Permittee shall equip and operatethe facility with a vapor control system thatreduces the total acid gas emissions to theoutdoor atmosphere by no less than 70percent by weight. This equipment shall bein operation at any time waste is beingcharged to the combustor. [N.J.A.C.7:27-22.16(e)]Operating Control Efficiency: Monitored bystack emission testing upon request of theDepartment, based on the average of three1-hour tests. [N.J.A.C. 7:27-22.16(o)]Operating Control Efficiency:Recordkeeping by stack test results uponrequest of the Department. [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Refer to stack testingrequirements specified in this permit.[N.J.A.C. 7:27-22.16(o)]35Scrubbing Medium Inlet Pressure <= 3,600inches. [N.J.A.C. 7:27-22.16(a)]Scrubbing Medium Inlet Pressure:Monitored by pressure measurement deviceeach week during operation when inoperation. [N.J.A.C. 7:27-22.16(o)]Scrubbing Medium Inlet Pressure:Recordkeeping by manual logging ofparameter daily. Records shall be kept in apermanently bound logbook or in readilyavailable computer files. [N.J.A.C.7:27-22.16(o)]None.36SO2: monitor shall assure that acid gasabsorber system is operating correctly.[N.J.A.C. 7:27-22.16(a)]SO2: Monitored by continuous emissionmonitoring system continuously. [N.J.A.C.7:27-22.16(o)]SO2: Recordkeeping by manual logging ofparameter or storing data in a computer datasystem each week during operation.[N.J.A.C. 7:27-22.16(o)]None.Page 62 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement37The particulate control device CD1004 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Flakt ESPUnit Type: 3-stage plateCapacity: 184,672 acfmNumber of plates: 37Number of fields: 3Plate Surf Area: 1190 ft2Design efficiency: 99.9%[N.J.A.C. 7:27-22.16(a)]None.None.None.38Particulate Emissions: Continuous opacitymonitor shall assurethat electrostaticprecipitator system is operating correctly.[N.J.A.C. 7:27-22.16(a)]Particulate Emissions: Monitored bycontinuous emission monitoring systemcontinuously. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bymanual logging of parameter or storing datain a computer data system each week duringoperation. [N.J.A.C. 7:27-22.16(o)]None.39The NOx control device CD1007 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [frommodification BOP090001)Reagent: Ammonium hydroxideMinimum reagent concentration: 19 %Min/Max reagent flow rate: 0.2 - 7 gpmMax. NOx/reagent mol ratio: 0.8Reagent injectors: 54Max. Ammonia slip: < 50 ppmFlue Gas temperature: 1600 - 1900 deg FDesign efficiency: 50%[N.J.A.C. 7:27-22.16(a)]None.None.None.40Nitrogen oxides (NOx):monitor shall assurethat absorber system is operating correctly.[N.J.A.C. 7:27-22.16(a)]Nitrogen oxides (NOx): Monitored bycontinuous emission monitoring systemcontinuously. [N.J.A.C. 7:27-22.16(o)]Nitrogen oxides (NOx): Recordkeeping bymanual logging of parameter or storing datain a computer data system each week duringoperation. [N.J.A.C. 7:27-22.16(o)]None.Page 63 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement41The mercury control device CD1010 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Norit Americas Carbon InjectionAdsorbent: Carbon (Lignite, DARCO FGD,or equiv.)Injection rate: 0 - 100 lbs/hrDesign efficiency: 80%[N.J.A.C. 7:27-22.16(a)]None.None.None.Page 64 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U1 Municipal Waste Combustors (E1, E2 & E3) - Subject to NSPS Subparts Cb and 40 CFR 62 Subpart FFFOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1EMERGENCY MALFUNCTION: Anemergency malfunction means any suddenand unavoidable failure to the equipment orcontrol apparatus to operate in a normalmanner. Malfunctions that are causedentirely or in part by improperly designedequipment, lack of preventativemaintenance, careless or improperoperation, operator error, or any preventableupset condition or preventable equipment orcontrol apparatus breakdown shall not beconsidered emergency malfunctions. In anyenforcement proceeding the Permitteeseeking to establish the occurrence of anemergency malfunction has the burden ofproof.[N.J.A.C. 7:27-22.16(e)]None.None.Submit a report: As per the approvedschedule. For a permittee to claim anemission limit exceedance is due to anemergency malfunction the Permittee mustsubmit a written written preliminary noticeto the Department by 5:00 pm of the secondfull working day following the incident.This preliminary notice must include:A description of the malfunction andhow it resulted in a contravention.A description of the measures taken tocorrect the conditions causing thecontravention.A description of the measures taken tominimize the excess emissions includingcurtailment or shutdown of the combustor.This provision does not relieve thePermittee from immediately notifying theDepartment of any release of aircontaminants in a quantity or concentrationwhich poses a potential threat to publichealth.wealth, or the environment, or whichmight result in citizen complaints, pursuantto N.J.S.A. 26:2C-19(e). [N.J.A.C.7:27-22.16(e)]2EMERGENCY MALFUNCTION:The Department will review the EmergencyMalfunction asserted by the facility. If theDepartment deems that any EmergencyMalfuntion was asserted incorrectly, theDepartment will reject the claim and takeappropriate enforcement action.[N.J.A.C. 7:27-22.16(a)]None.None.None.OS2 Operation of MWC # 1 under Malfunction conditions, OS4 Operation of MWC # 2 under Malfunction conditions, OS6 Operationof MWC # 3 under Malfunction conditionsPage 65 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3EMERGENCY MALFUNCTION:To obtain malfunction allowances, thefacility must:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissionsduring malfunction periods;d. Identify and take steps to preventmalfunctions from occuring in future; ande. Report malfunctions in accordance withthe reporting requirements of this permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.4EMERGENCY MALFUNCTION:Within thirty days of an emergencymalfunction, the Permittee shall submit tothe Department certified information whichidentifies the contravention and includes thefollowing:Copies of relevant operating dataincluding but not limited to continuousmonitoring data or portions of logbooksthat show the malfunction to be sudden andunavoidable. Relevant data shall include at aminimum data recorded one hour before,during, and one hour after the malfunction.List of the actions taken to prevent thepotential for the malfunction from occuringin the future.Certification in accordance withN.J.A.C. 7:27-1.39 that the malfunction didnot occur as a result of: improperly designedequipment, lack of preventativemaintenance, careless or improperoperation, or operator error, and certificationthat the information contained in thepreliminary notice is correct. If theinformation submitted in the preliminarynotice is inaccurate, a certified revision ofthe notice shall be submitted. [N.J.A.C.7:27-22.16(e)]None.None.None.Page 66 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5EMERGENCY MALFUNCTION:The duration of emission excursions causedby malfunctions shall not exceed thefollowing limits per occurence and percentof operating time:SO2 180min. 2%CO 60min 0.2%NOx 180min 2%[N.J.A.C. 7:27-22.16(e)]Monitored by continuous emission monitorupon occurrence of event (and hour timemonitor). [N.J.A.C. 7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. Data may beperiodically printed and maintained reliablyin a log book on site. [N.J.A.C.7:27-22.16(o)]None.6EMERGENCY MALFUNCTION:The duration of operating requirementexcursions caused by malfunctions shall notexceed the following limits per occurenceand percent of operating time:Temperature 60min. 0.1%[N.J.A.C. 7:27-22.16(e)]Monitored by parametric monitoring systemupon occurrence of event (temperaturemonitor and hour time monitor). [N.J.A.C.7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. Data may beperiodically printed and maintained reliablyin a log book on site. [N.J.A.C.7:27-22.16(o)]None.7EMERGENCY MALFUNCTION:Neither the time , nor the emissions, duringthe periods of emergency malfunctionsmeeting the above criteria shall be used inthe calculation of emission levels forcomparison to allowable emission limits.[N.J.A.C. 7:27-22.16(e)]None.None.None.8EMERGENCY MALFUNCTION:Malfunctions resulting in an excursion of anemission limit with an averaging time of lessthan or equal to one hour shall be deemed tohave occured during the entire applicableaveraging time of that emission limit.Malfunction resulting in an excursion of anemission limit with an averaging time ofgreater than one hour shall be deemed tohave occured only during the hours of themalfunction. [N.J.A.C. 7:27-22.16(e)]None.None.None.9EMERGENCY MALFUNCTION:Any visible emission caused by amalfunction shall not exceed an average of10% opacity in any 6 minute block period,as determined by the continuous emissionmonitoring equipment or USEPA ReferenceMethod 9. [N.J.A.C. 7:27-22.16(e)]Monitored by continuous opacity monitorupon occurrence of event, based on 6 minuteblocks. [N.J.A.C. 7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.Page 67 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U1 Municipal Waste Combustors (E1, E2 & E3) - Subject to NSPS Subparts Cb and 40 CFR 62 Subpart FFFOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The owner or operator of any sourceoperation that has the potential to emit atleast three pounds per hour and is notregulated elsewhere in subchapter16 shall:1. submit a demonstration that the sourceoperation is served by a control apparatusthat collects at least 90 percent by weight ofthe VOC emissions and prevents from beingdischarged into the outdoor atmosphere atleast 90 percent by weight of the VOCcollected, or that the owner or operator hasimplemented pollution prevention measuresthat achieve at least the same level of VOCemission reductions, or2. a proposed alternative VOC control plan,or3. demonstrate that the actual annualemissions of VOC from the facility in 1990and each year thereafter were less than 25tons and the operator intends to reduce thefacility's potential to emit VOC to less than25 tons per year, in accordance withN.J.A.C. 7:27-16-17(f).[N.J.A.C. 7:27-16.17(b)] and [N.J.A.C.7:27-16.17(f)]None.None.None.2Unless otherwise specified, the emissionlimits specified under this operating scenarioshall apply at all times, except for start-upand shutdown periods. [N.J.A.C.7:27-22.16(e)]None.None.None.3Maximum emission rate of Non-MethaneHydrocarbons as Methane, VOC (Total) <=6.3 lb/hr. [N.J.A.C. 7:27-22.16(e)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]OS7 Operation of MWC # 1 at Maximum Input(423 MMBtu/hr) usingCovanta Low-NOx (LN) Control,OS8 Operationof MWC # 2 atMaximum Input (423 MMBtu/hr) using Covanta Low-NOx (LN) Control, OS9 Operation of MWC # 3 at Maximum Input (423MMBtu/hr) using Covanta Low-NOx (LN) ControlPage 68 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4Maximum concentration of Non-MethaneHydrocarbons as Methane, VOC (Total) <=66 ppmvd @ 7% O2. [N.J.A.C.7:27-22.16(e)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]5NOx (Total) <= 95 lb/hr frompreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Monitored by stack emissiontesting every 5 years, based on the averageof three 1-hour tests. Three test runs mustbe conducted oneach unit, with ammoniainjection, to determine compliance.[N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by stack testresults every 5 years. [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]6NOx (Total) <= 300 ppmvd @ 7% O2. Theemission limitation shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitor continuously, based on a 1hour block average , beginning and endingon the hour. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by strip chartor data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]None.7NOx (Total) <= 155 ppmvd @ 7% O2. Theemission limitation shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitor continuously, based on a24 hour period block, beginning and endingat midnight. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by strip chartor data acquisition (DAS) systemcontinuously. [N.J.A.C. 7:27-22.16(e)]None.8CO <= 126 lb/hr from preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]CO: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]CO: Recordkeeping by stack test resultsupon occurrence of event. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]9CO <= 400 ppmvd @ 7% O2. The emissionlimitation shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]CO: Monitored by continuous emissionmonitor continuously, based on a 1 hourblock average , beginning and ending on thehour. [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. See most stringent limitationspecified in this permit. [N.J.A.C.7:27-22.16(e)]Page 69 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10CO <= 100 ppmvd @ 7% O2. The emissionlimitation shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]CO: Monitored by continuous emissionmonitor continuously, based on a 96 hourrolling average based on a 1 hour blockaverage beginning and ending on the hour.[N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. See most stringent limitationspecified in this permit. [N.J.A.C.7:27-22.16(e)]11The CO and NOx emission limits specifiedin permit condition, for normal steady stateoperation shall not apply during periods,including warm-up periods, when no wasteis burned and fossil fuel is being combusted.Only auxiliary fuel (fuel oil) shall becombusted during warm-up periods, and nomunicipal solid waste shall combusted. Thewarm-up period begins upon initiation ofauxiliary fuel (fuel oil) combustion in thefurnace. The duration of exemption fromemission limits during these periods shallnot exceed 10 consecutivehours perwarm-up period. [N.J.A.C. 7:27-22.16(e)]None.None.None.12SO2 <= 75.8 lb/hr. [N.J.A.C. 7:27-22.16(e)]SO2: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs [From BOP080001.]. [N.J.A.C.7:27-22.16(o)]SO2: Recordkeeping by stack test resultsupon occurrence of event [FromBOP080001.]. [N.J.A.C. 7:27-22.16(o)]None.13SO2 <= 94 ppmvd @ 7% O2. This limitshall not apply for 1-hour block periodsduring which the average concentration ofSO2 (ppmdv@7%O2) in the stack gas isless than 30% of the average concentrationof SO2 (ppmdv@7%O2) at the inlet to theacid gas control equipment. [N.J.A.C.7:27-22.16(e)]SO2: Monitored by continuous emissionmonitor continuously, based on a 1 hourblock average , beginning and ending on thehour. [N.J.A.C. 7:27-22.16(e)]SO2: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]None.14SO3 and H2SO4, as converted andexpressed as H2SO4 <= 4 lb/hr. [N.J.A.C.7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 70 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15Particulate Emissions <= 9.8 lb/hr frompreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]16Particulate Emissions <= 0.014 gr/dscf @7% O2. [N.J.A.C. 7:27-22.16(e)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]17Particulate Emissions <= 0.028 gr/dscf @7% O2 for each individual test run,including test runs during which sootblowing is performed. [N.J.A.C.7:27-22.16(e)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]18PM-10 (Total) <= 22.8 lb/hr Hourlyemission rate established from stack test(s)results. [Modification BOP090001].[N.J.A.C. 7:27-22.16(a)]PM-10 (Total): Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]PM-10 (Total): Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]19Any visible emissions shall not exceed anaverage Opacity <= 10 %. [N.J.A.C.7:27-22.16(e)]Opacity: Monitored by continuous emissionmonitor continuously, based on 6 minuteblocks. The discrete block average willbegin on the hour. [N.J.A.C. 7:27-22.16(e)]Opacity: Recordkeeping by strip chart ordata acquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(e)]Notify by phone: Upon occurrence of event.Any non-compliance shall be reported.[N.J.A.C. 7:27-22.16(e)]20Arsenic compounds <= 0.0051 lb/hr.[N.J.A.C. 7:27-22.16(e)]Arsenic compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Arsenic compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]21Beryllium Compounds <= 0.00025 lb/hr.[N.J.A.C. 7:27-22.16(e)]Beryllium compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Beryllium compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]22Cadmium compounds <= 0.043 lb/hr.[N.J.A.C. 7:27-22.16(e)]Cadmium compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Cadmium compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 71 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement23Chromium compounds <= 0.012 lb/hr.[N.J.A.C. 7:27-22.16(e)]Chromium compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Chromium compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]24HCl Emissions <= 21.6 lb/hr. [N.J.A.C.7:27-22.16(e)]HCl Emissions: Monitored by stackemission testing annually, based oneach ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]HCl Emissions: Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]25HCl Emissions <= 47 ppmvd @ 7% O2.This limit shall not apply for 1-hour blockperiods during which the averageconcentration of HCl (ppmdv @ 7% O2) inthe stack gas is less than 10% of the averageconcentration of HCl (ppmdv @ 7% O2) atthe inlet to the acid gas control equipment.[N.J.A.C. 7:27-22.16(e)]HCl Emissions: Monitored by stackemission testing annually, based oneach ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]HCl Emissions: Recordkeeping by stack testresults upon occurrence of event. See stacktesting requirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]26Hydrogen fluoride <= 0.82 lb/hr. [N.J.A.C.7:27-22.16(e)]Hydrogen fluoride: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Hydrogen fluoride: Recordkeeping by stacktest results upon occurrence of event. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]27Lead compounds <= 0.5 lb/hr. [N.J.A.C.7:27-22.16(e)]Lead compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Lead compounds: Recordkeeping by stacktest results upon occurrence of event. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]28Mercury compounds <= 0.053 lb/hr inaccordance with the July 27,1997preconstruction permit and confirming letterdated August 27, 2002. [N.J.A.C.7:27-22.16(e)]Mercury compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]Mercury compounds: Recordkeeping bystack test results upon occurrence of event.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]29Nickel compounds <= 0.0033 lb/hr.[N.J.A.C. 7:27-22.16(e)]Nickel compounds: Monitored by stackemission testing prior to permit renewal,based on the average of three Departmentvalidated stack test runs. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Nickel compounds: Recordkeeping by stacktest results upon occurrence of event. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 72 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement30TCDD Emissions (2,3,7,8-) <= 0.00001lb/hr. [N.J.A.C. 7:27-22.16(e)]TCDD Emissions (2,3,7,8-): Monitored bystack emission testing annually, based on theaverage of three Department validated stacktest runs. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]TCDD Emissions (2,3,7,8-): Recordkeepingby stack test results upon occurrence ofevent. See stack testing requirements in U1OS0. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]31Polycyclic aromatic hydrocarbons, orPolycyclic organic matter <= 0.29 lb/hr.[N.J.A.C. 7:27-22.16(a)]Polycyclic organic matter: Monitored bystack emission testing prior to permitrenewal, based on the average of threeDepartment validated stack test runs. Seestack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Polycyclic organic matter: Recordkeepingby stack test results upon occurrence ofevent. See stack testing requirements in U1OS0. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]32Emissions of benzo(a) pyrene, carbontetrachloride, formaldehyde,perchloroethylene (tetrachloroethylene),trichloroethylene and vinyl chloride shall bebelow the reporting threshold of N.J.A.C.7:27-22, Tables A & B and must bemeasured using methods approved by DEP.[N.J.A.C. 7:27-22.16(e)]Monitored by stack emission testing prior topermit renewal, based on the average ofthree Department validated stack test runs.See stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]Recordkeeping by stack test results uponoccurrence of event. See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]33The acid gas control device CD1001 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Absorber fluid medium: Lime solutionPump Disch Press: 0 - 300 Ft H2OMax. solution flow rate: 30 gpmFlow monitor: Bailey Net 90 Control SystemGas flow rate: 215-315,000 acfmAbsorber inlet/outlet pressure: 5.5 & 6inches w.c.Gas temperature: 302 - 491 deg FDesign efficiency: 70% [N.J.A.C.7:27-22.16(a)]None.None.None.34Operating Control Efficiency >= 70 %control. Permittee shall equip and operatethe facility with a vapor control system thatreduces the total acid gas emissions to theoutdoor atmosphere by no less than 70percent by weight. This equipment shall bein operation at any time waste is beingcharged to the combustor. [N.J.A.C.7:27-22.16(e)]Operating Control Efficiency: Monitored bystack emission testing upon request of theDepartment, based on the average of three1-hour tests. [N.J.A.C. 7:27-22.16(o)]Operating Control Efficiency:Recordkeeping by stack test results uponrequest of the Department. [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Refer to stack testingrequirements specified in this permit.[N.J.A.C. 7:27-22.16(o)]Page 73 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement35Scrubbing Medium Inlet Pressure <= 3,600inches. [N.J.A.C. 7:27-22.16(a)]Scrubbing Medium Inlet Pressure:Monitored by pressure measurement deviceeach week during operation when inoperation. [N.J.A.C. 7:27-22.16(o)]Scrubbing Medium Inlet Pressure:Recordkeeping by manual logging ofparameter daily. Records shall be kept in apermanently bound logbook or in readilyavailable computer files. [N.J.A.C.7:27-22.16(o)]None.36SO2: monitor shall assure that acid gasabsorber system is operating correctly.[N.J.A.C. 7:27-22.16(a)]SO2: Monitored by continuous emissionmonitoring system continuously. [N.J.A.C.7:27-22.16(o)]SO2: Recordkeeping by manual logging ofparameter or storing data in a computer datasystem each week during operation.[N.J.A.C. 7:27-22.16(o)]None.37The particulate control device CD1004 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Flakt ESPUnit Type: 3-stage plateCapacity: 184,672 acfmNumber of plates: 37Number of fields: 3Plate Surf Area: 1190 ft2Design efficiency: 99.9%[N.J.A.C. 7:27-22.16(a)]None.None.None.38Particulate Emissions: Continuous opacitymonitor shall assurethat electrostaticprecipitator system is operating correctly.[N.J.A.C. 7:27-22.16(a)]Particulate Emissions: Monitored bycontinuous emission monitoring systemcontinuously. [N.J.A.C. 7:27-22.16(o)]Particulate Emissions: Recordkeeping bymanual logging of parameter or storing datain a computer data system each week duringoperation. [N.J.A.C. 7:27-22.16(o)]None.39The NOx control device CD1007 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [frommodification BOP090001)Reagent: Ammonium hydroxideMinimum reagent concentration: 19 %Min/Max reagent flow rate: 0.2 - 7 gpmMax. NOx/reagent mol ratio: 0.8Reagent injectors: 54Max. Ammonia slip: < 50 ppmFlue Gas temperature: 1600 - 1900 deg FDesign efficiency: 50%[N.J.A.C. 7:27-22.16(a)]None.None.None.Page 74 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement40Nitrogen oxides (NOx):monitor shall assurethat absorber system is operating correctly.[N.J.A.C. 7:27-22.16(a)]Nitrogen oxides (NOx): Monitored bycontinuous emission monitoring systemcontinuously. [N.J.A.C. 7:27-22.16(o)]Nitrogen oxides (NOx): Recordkeeping bymanual logging of parameter or storing datain a computer data system each week duringoperation. [N.J.A.C. 7:27-22.16(o)]None.41The mercury control device CD1010 shallcomply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Norit Americas Carbon InjectionAdsorbent: Carbon (Lignite, DARCO FGD,or equiv.)Injection rate: 0 - 100 lbs/hrDesign efficiency: 80%[N.J.A.C. 7:27-22.16(a)]None.None.None.Page 75 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U6 Lime Storage Silo A (E4) controlled by filter CD1013, U7 Lime Storage Silo B (E5) controlled by filter CD1014, U8 Lime Storage Silo C (E6)controlled by filter CD1015Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum allowable particulate emissionrate from PT4 based on 0.02 grains per SCF.Particulate Emissions <= 0.5 lb/hr.[N.J.A.C. 7:27- 6.2(a)]None.None.None.2The owner or operator shall not use thisemission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period longer than three minutesin any consecutive 30-minute period.[N.J.A.C. 7:27-6.2(d)] and [N.J.A.C. 7:27-6.2(e)]None.None.None.3The permittee shall not use the equipment ina manner which will cause visible emissions,exclusive of condensed water vapor.[N.J.A.C. 7:27-22.16(e)]None.None.None.4Annual emission limit from thepreconstruction permit. TSP <= 0.876tons/yr. [N.J.A.C. 7:27-22.16(e)]None.None.None.5Annual emission limit from the operatingpermit. application. PM-10 (Total) <= 0.876tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.6Maximum emission rate imposed frompreconstruction permit. TSP <= 0.2 lb/hr.[N.J.A.C. 7:27-22.16(e)]None.None.None.7PM-10 (Total) <= 0.2 lb/hr Maximumemission rate from operating permitapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.8All particulate emissions from each emissionunit shall be exhausted through a dustcollector (CD1013, CD1014, or CD1015, asappropriate.) [N.J.A.C. 7:27-22.16(e)]None.None.None.OS SummaryPage 76 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9The owner or operator shall inspect andmaintain the dust collector and replace thefilter media on a schedule necessary toachieve the required particulate controleffeciency as specified by the manufacturer.[N.J.A.C. 7:27-22.16(a)]Monitored by visual determination onceevery 2 weeks. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event , or manually in apermanently bound logbook. Recordeachinspection and maintenance event in apermanently bound logbook or readilyaccessible computer memory. [N.J.A.C.7:27-22.16(o)]None.10The control device CD1013 shall complywith the design specified in the controldevice details section of the application foroperating permit [from renewal applicationBOP080001)Griffen Model DF44Number of bags - 54Bag size - 7.6 ft2Total Bag Area - 375 FT2Bag Fabric - PolypropyleneFabric Weave - non-wovenMaximum Air Flow/Cloth Area: 5.28 to 1Method of Bag Cleaning - mechanicalshakingPressure drop across bag: 4 - 6 inches w.c.Design efficiency: ??% [N.J.A.C.7:27-22.16(a)]None.None.None.Page 77 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U9 Lime Slaker Vent A (E9) , U10 Lime Slaker Vent B (E10)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum allowable particulate emissionrate from PT9 based on 0.02 grains per SCF.Particulate Emissions <= 0.5 lb/hr.[N.J.A.C. 7:27- 6.2(a)]None.None.None.2The owner or operator shall not use thisemission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period longer than three minutesin any consecutive 30-minute period.[N.J.A.C. 7:27-6.2(d)] and [N.J.A.C. 7:27-6.2(e)]None.None.None.3The permittee shall not use the equipment ina manner which will cause visible emissions,exclusive of condensed water vapor.[N.J.A.C. 7:27-22.16(e)]None.None.None.4Annual emission limit from thepreconstruction permit. TSP <= 0.027tons/yr. [N.J.A.C. 7:27-22.16(e)]None.None.None.5Annual emission limit from the operatingpermit. application. PM-10 (Total) <= 0.027tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.6Maximum emission rate imposed frompreconstruction permit. ParticulateEmissions <= 0.0063 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.7PM-10 (Total) <= 0.0063 lb/hr Maximumemission rate from operating permitapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.OS SummaryPage 78 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U11 Activated Carbon Storage Silo (E14) controlled by filter CD1020Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Particulate Emissions <= 0.5 lb/hr.Maximum allowable particulate emissionrate from source emission point based on99% efficiency of collection or based on0.02 grains per SCF of stack gas flow asdetermined in the Table at N.J.A.C.7:27-6.2(a). [N.J.A.C. 7:27- 6.2(a)]None.None.None.2The owner or operator shall not use thisemission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period longer than three minutesin any consecutive 30-minute period.[N.J.A.C. 7:27-6.2(d)] and [N.J.A.C. 7:27-6.2(e)]None.None.None.3The permittee shall not use the equipment ina manner which will cause visible emissions,exclusive of condensed water vapor.[N.J.A.C. 7:27-22.16(e)]None.None.None.4Annual emission limit from thepreconstruction permit. TSP <= 0.9 tons/yr.[N.J.A.C. 7:27-22.16(e)]None.None.None.5Annual emission limit from the operatingpermit. application. PM-10 (Total) <= 0.9tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.6Maximum emission rate imposed frompreconstruction permit. TSP <= 0.2 lb/hr.[N.J.A.C. 7:27-22.16(e)]None.None.None.7Maximum emission rate from operatingpermit application. PM-10 (Total) <= 0.2lb/hr. [N.J.A.C. 7:27-22.16(a)]None.None.None.8All particulate emissions from this emissionunit shall be exhausted through a dustcollector (CD1020). [N.J.A.C.7:27-22.16(e)]None.None.None.OS SummaryPage 79 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9The owner or operator shall inspect andmaintain the dust collector and replace thefilter media on a schedule necessary toachieve the required particulate controleffeciency as specified by the manufacturer.[N.J.A.C. 7:27-22.16(a)]Monitored by visual determination onceevery 2 weeks. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event , or manually in apermanently bound logbook. Recordeachinspection and maintenance event. [N.J.A.C.7:27-22.16(o)]None.10The control device CD1020 shall complywith the design specified in the controldevice details section of the application foroperating permit [from renewal applicationBOP080001)Number of bags - 25Bag size - 10.6 ft2Total Bag Area - 265 ft2Bag Fabric - PolyesterFabric Weave - feltFabric finish: plainMaximum Air Flow/Cloth Area: 1 to 1Method of Bag Cleaning - pulse jetPressure drop across bag: 4 - 6 inches w.c.Design efficiency: 99?? % [N.J.A.C.7:27-22.16(a)]None.None.None.Page 80 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U12 Flyash Conditioning Room (E12, E13) controlled by filters CD1017, 1018 & 1019Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum allowable particulate emissionrate from source emission point based on99% efficiency of collection or based on0.02 grains per SCF of stack gas flow asdetermined in the Table at N.J.A.C.7:27-6.2(a). Particulate Emissions <= 0.5lb/hr. [N.J.A.C. 7:27- 6.2(a)]None.None.None.2The owner or operator shall not use thisemission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period longer than three minutesin any consecutive 30-minute period.[N.J.A.C. 7:27-6.2(d)] and [N.J.A.C. 7:27-6.2(e)]None.None.None.3Annual emission limit from thepreconstruction permit. TSP <= 0.131tons/yr. [N.J.A.C. 7:27-22.16(e)]None.None.None.4Annual emission limit from the operatingpermit. application. PM-10 (Total) <= 0.15tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.5Maximum emission rate imposed frompreconstruction permit. ParticulateEmissions <= 0.015 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.6PM-10 (Total) <= 0.015 lb/hr Maximumemission rate from operating permitapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.7All particulate emissions from this emissionunit shall be exhausted through dustcollectors CD1017 or CD1018 and thenexhaust the building through CD1019.[N.J.A.C. 7:27-22.16(e)]None.None.None.8The owner or operator shall inspect andmaintain the dust collectors and replace thefilter media on a schedule necessary toachieve the required particulate controleffeciency as specified by the manufacturer.[N.J.A.C. 7:27-22.16(a)]Monitored by visual determination onceevery 2 weeks. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by manual logging ofparameter upon occurrence of event.Record each inspection and maintenanceevent in a permanently bound logbook orreadily accessible computer memory.[N.J.A.C. 7:27-22.16(o)]None.OS SummaryPage 81 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9The control devices CD1017 & CD1018shall comply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Number of bags - 9Bag size - 7.2 ft2Total Bag Area - 65 FT2Bag Fabric - Polyester feltFabric Weave - non-wovenMaximum Air Flow/Cloth Area: 5.2 to 1Method of Bag Cleaning - pulse jetPressure drop across bag: 3 - 6 inches w.c.Design efficiency: 99.8 % [N.J.A.C.7:27-22.16(a)]None.None.None.10The control device CD1019 shall complywith the design specified in the controldevice details section of the application foroperating permit [from renewal applicationBOP080001)Number of bags - 36Bag size - 10.6 ft2Total Bag Area - 382 FT2Bag Fabric - PolypropyleneFabric Weave - feltMaximum Air Flow/Cloth Area: 5.24 to 1Method of Bag Cleaning - pulse jetPressure drop across bag: 3 - 6 inches w.c.Design efficiency: 99.8 % [N.J.A.C.7:27-22.16(a)]None.None.None.Page 82 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U13 7.4 MMBtu/hr Diesel Engine-driven Emergency Generator (E7)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The permittee shall not use the equipment ina manner which will cause visible emissionsto exceed 20% opacity, exclusive of watervapor, for a period of more than 10consecutive seconds. [N.J.A.C. 7:27- 3.5]None.None.None.2Maximum emission rate from the table atN.J.A.C. 7:27-4.2(a), based on theMaximum Gross Heat input. ParticulateEmissions <= 4.2 lb/hr. [N.J.A.C. 7:27-4.2(a)]None.None.None.3The maximum allowable diesel fuel oilsulfur content is based on the geographiclocation of the facility (Essex County).Sulfur Content in Fuel <= 0.2 %. [N.J.A.C.7:27- 9.2(b)]Other: The permittee shall check the fuel oilsulfur content on the invoices/bills oflading.[N.J.A.C. 7:27- 9.2(b)].None.None.4The permittee shall not use the equipment ina manner which will cause visible emissionsto exceed 10% opacity, except for a periodof 30 minutes during startup and shutdownwhen opacity shall not exceed 20%,exclusive of water vapor [N.J.A.C.7:27-22.16(e)]None.None.None.5Maximum Gross Heat Input <= 7.4MMBTU/hr for engine-driven emergencygenerator from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Other: fuel burner rated capacity[N.J.A.C.7:27-22.16(o)].None.None.6Generator fuel limited to #2 fuel oil.[N.J.A.C. 7:27-22.16(a)]None.None.None.OS SummaryPage 83 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7The emergency generator shall be located atthe facility and produce mechanical orthermal energy, or electrical powerexclusively for use at the facility. Thisemergency generator shall be operated only:1. During the performance of normal testingand maintenance procedures, asrecommended in writing by themanufacturer and/or as required in writingby a Federal or State law or regulation,2. When there is power outage or theprimary source of mechanical or thermalenergy fails because of an emergency, or3. When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com)under the"emergency procedures" menu.[N.J.A.C. 7:27-19.1]Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem, the following information:1. For each time the emergency generator isspecifically operated for testing ormaintenance:i. The reason for its operation;ii. The date(s) of operation and the startup and shut down time;iii. The total operating time for testing ormaintenance based on the generator's hourmeter; andiv. The name of the operator; and2. If a voltage reduction is the reason for theuse of the emergency generator, a copy ofthe voltage reduction notification from PJMor other documentation of the voltagereduction.[N.J.A.C. 7:27-19.11].None.Page 84 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8This emergency generator shall not be used:1. For normal testing and maintenance ondays when the Department forecasts airquality anywhere in New Jersey to be"unhealthy for sensitive groups,""unhealthy," or "very unhealthy" as definedin the EPA's Air Quality Index athttp://airnow.gov/, as supplemented oramended and incorporated herein byreference, unless required in writing by aFederal or State law or regulation.Procedures for determining the air qualityforecasts for New Jersey are available at theDepartment's air quality permitting web siteathttp://www.state.nj.us/dep/aqpp/aqforecast;and2. As a source of energy or power after theprimary energy or power source has becomeoperable again. If the primary energy orpower source is under the control of theowner or operator of the emergencygenerator, the owner or operator shall makea reasonable, timely effort to repair theprimary energy or power source.[N.J.A.C. 7:27-19.2(d)]None.None.None.9The Permittee shall, once per month, recordthe total operating time from the generator'shour meter.[N.J.A.C. 7:27-19.11]Monitored by hour/time monitorcontinuously . [N.J.A.C. 7:27-22.16(o)]Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem the total operating time from thegenerator's hour meter. Once per month.[N.J.A.C. 7:27-19.11].None.Page 85 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10Hours of Operation <= 50 hr/yr. ThePermittee shall comply with the above hourper year limit for normal testing andmaintenance. [N.J.A.C. 7:27-22.16(a)]Hours of Operation: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]Other: The Permittee shall record thefollowing in either a logbook or computerdata system each time the emergencygenerator is operated for testing ormaintenance:1. The reason for its operation;2. The date(s) of operation and the start upand shut down time;3. The total operating time for testing ormaintenance based on the generator's hourmeter; and4. The name of the operator.[N.J.A.C. 7:27-19.11].None.11Hours of Operation <= 500 hr/yr. ThePermittee shall comply with the above hourper year limit for emergency use combinedwith normal testing and maintenance.[N.J.A.C. 7:27-22.16(a)]None.None.None.12VOC (Total) <= 0.183 tons/yr. Annualemission limit based on 500 hours per yearof operation. [N.J.A.C. 7:27-22.16(a)]None.None.None.13NOx (Total) <= 6.53 tons/yr. Annualemission limit based on 500 hours per yearof operation. [N.J.A.C. 7:27-22.16(a)]None.None.None.14CO <= 1.7 tons/yr. Annual emission limitbased on 500 hours per year of operation.[N.J.A.C. 7:27-22.16(a)]None.None.None.15SO2 <= 0.392 tons/yr. Annual emissionlimit based on 500 hours per year ofoperation. [N.J.A.C. 7:27-22.16(a)]None.None.None.16TSP <= 0.653 tons/yr. Annual emissionlimit based on 500 hours per year ofoperation. [N.J.A.C. 7:27-22.16(a)]None.None.None.17PM-10 (Total) <= 0.653 tons/yr. Annualemission limit based on 500 hours per yearof operation. [N.J.A.C. 7:27-22.16(a)]None.None.None.Page 86 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U14 1.59 MMBtu/hr Diesel Engine-driven Emergency Fire Pump (E8)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The permittee shall not use the equipment ina manner which will cause visible emissionsto exceed 20% opacity, exclusive of watervapor, for a period of more than 10consecutive seconds. [N.J.A.C. 7:27- 3.5]None.None.None.2Maximum emission rate from the table atN.J.A.C. 7:27-4.2(a), based on theMaximum Gross Heat input. ParticulateEmissions <= 4.2 lb/hr. [N.J.A.C. 7:27-4.2(a)]None.None.None.3The maximum allowable diesel fuel oilsulfur content is based on the geographiclocation of the facility (Essex County).Sulfur Content in Fuel <= 0.2 %. [N.J.A.C.7:27- 9.2(b)]Other: The permittee shall check the fuel oilsulfur content on the invoices/bills oflading.[N.J.A.C. 7:27- 9.2(b)].None.None.4The permittee shall not use the equipment ina manner which will cause visible emissionsto exceed 10% opacity, except for a periodof 30 minutes during startup and shutdownwhen opacity shall not exceed 20%,exclusive of water vapor [N.J.A.C.7:27-22.16(e)]None.None.None.5Maximum Gross Heat Input <= 1.59MMBTU/hr (HHV) for engine-driven firewater pump from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Other: fuel burner rated capacity[N.J.A.C.7:27-22.16(o)].None.None.6Engine fuel limited to #2 fuel oil. [N.J.A.C.7:27-22.16(a)]None.None.None.OS SummaryPage 87 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7The fire water pump shall be located at thefacility and produce mechanical powerexclusively for use at the facility. Thispump shall be operated only:1. During the performance of normal testingand maintenance procedures, asrecommended in writing by themanufacturer and/or as required in writingby a Federal or State law or regulation,2. When there is a fire emergency or theprimary source of mechanical energy failsbecause of an emergency, or3. When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com)under the"emergency procedures" menu.[N.J.A.C. 7:27-19.1]Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem, the following information:1. For each time the fire water pump isspecifically operated for testing ormaintenance:i. The reason for its operation;ii. The date(s) of operation and the startup and shut down time;iii. The total operating time for testing ormaintenance based on the fire water pump'shour meter; andiv. The name of the operator; and2. If a voltage reduction is the reason for theuse of the fire water pump, a copy of thevoltage reduction notification from PJM orother documentation of the voltagereduction.[N.J.A.C. 7:27-19.11].None.Page 88 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8This fire water pump shall not be used:1. For normal testing and maintenance ondays when the Department forecasts airquality anywhere in New Jersey to be"unhealthy for sensitive groups,""unhealthy," or "very unhealthy" as definedin the EPA's Air Quality Index athttp://airnow.gov/, as supplemented oramended and incorporated herein byreference, unless required in writing by aFederal or State law or regulation.Procedures for determining the air qualityforecasts for New Jersey are available at theDepartment's air quality permitting web siteathttp://www.state.nj.us/dep/aqpp/aqforecast;and2. As a source of energy or power after theprimary energy or power source has becomeoperable again. If the primary energy orpower source is under the control of theowner or operator of the fire water pump,the owner or operator shall make areasonable, timely effort to repair theprimary energy or power source.[N.J.A.C. 7:27-19.2(d)]None.None.None.9The Permittee shall, once per month, recordthe total operating time from the engine'shour meter.[N.J.A.C. 7:27-19.11]Monitored by hour/time monitorcontinuously . [N.J.A.C. 7:27-22.16(o)]Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem the total operating time from the firewater pump's hour meter. Once per month.[N.J.A.C. 7:27-19.11].None.Page 89 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10Hours of Operation <= 50 hr/yr. ThePermittee shall comply with the above hourper year limit for normal testing andmaintenance. [N.J.A.C. 7:27-22.16(a)]Hours of Operation: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]Other: The Permittee shall record thefollowing in either a logbook or computerdata system each time the fire water pump isoperated for testing or maintenance:1. The reason for its operation;2. The date(s) of operation and the start upand shut down time;3. The total operating time for testing ormaintenance based on the fire water pump'shour meter; and4. The name of the operator.[N.J.A.C. 7:27-19.11].None.11Hours of Operation <= 500 hr/yr. ThePermittee shall comply with the above hourper year limit for emergency use combinedwith normal testing and maintenance.[N.J.A.C. 7:27-22.16(a)]None.None.None.12VOC (Total) <= 0.105 tons/yr. Annualemission limit based on 500 hours per yearof operation. [N.J.A.C. 7:27-22.16(a)]None.None.None.13NOx (Total) <= 1.3 tons/yr. Annualemission limit based on 500 hours per yearof operation. [N.J.A.C. 7:27-22.16(a)]None.None.None.14CO <= 0.286 tons/yr. Annual emission limitbased on 500 hours per year of operation.[N.J.A.C. 7:27-22.16(a)]None.None.None.15SO2 <= 0.087 tons/yr. Annual emissionlimit based on 500 hours per year ofoperation. [N.J.A.C. 7:27-22.16(a)]None.None.None.16TSP <= 0.094 tons/yr. Annual emissionlimit based on 500 hours per year ofoperation. [N.J.A.C. 7:27-22.16(a)]None.None.None.17PM-10 (Total) <= 0.094 tons/yr. Annualemission limit based on 500 hours per yearof operation. [N.J.A.C. 7:27-22.16(a)]None.None.None.Page 90 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U15 Ash Conveyance System (E16, E17, E18) controlled by filters CD1017, 1018 & 1019Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum allowable particulate emissionrate from source emission point based on99% efficiency of collection or based on0.02 grains per SCF of stack gas flow asdetermined in the Table at N.J.A.C.7:27-6.2(a). Particulate Emissions <= 1.62lb/hr. [N.J.A.C. 7:27- 6.2(a)]None.None.None.2The permittee shall not use the equipment ina manner which will cause visible emissions,exclusive of condensed water vapor.[N.J.A.C. 7:27-22.16(e)]Monitored by visual determination eachmonth during operation, based on aninstantaneous determination. The permitteeshall conduct visual opacity inspectionsduring daylight hours. Visual inspectionsshall consist of a visual survey to identify ifthe stack has visible emissions, (other thancondensed water vapor), greater than theprescribed standard. If visible emissions areobserved, the permittee shall (1) Verify thatthe equipment and/or control device causingthe emission is operating according tomanufacturer's specifications and theoperating permit compliance plan. If theequipment or control device is not operatingproperly, the permittee shall take correctiveaction immediately to eliminate the excessemissions and 2) If the corrective actiontaken does not correct the opacity problemwithin 24 hours, the applicant shall performa check via a certified opacity reader, inaccordance with N.J.A.C. 7:27B-2. Such atest shall be conducted onceeach day untilcorrective action is taken to successfullycorrect the opacity problem. [N.J.A.C.7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage each monthduring operation , or manually in apermanently bound logbook. The permitteemust retain the following records: (1) Dateand time of inspection; (2) Emission pointnumber; (3) Operational status ofequipment; (4) Observed results andconclusions; (5) Description of correctiveaction taken if needed; (6) Date and timeopacity problem was solved, if applicable;(7) N.J.A.C. 7:27B-2 results, if conducted,and (8) Name of person(s) conductinginspection. [N.J.A.C. 7:27-22.16(e)]Other (provide description): Uponoccurrence of event the permittee mustreport any continuing permit violation to NJDEP pursuant to N.J.A.C. 7:27-22.19.[N.J.A.C. 7:27-22.19]3Annual emission limit from thepreconstruction permit. TSP <= 2.2 tons/yr.[N.J.A.C. 7:27-22.16(e)]None.None.None.4Annual emission limit from the operatingpermit. application. PM-10 (Total) <= 2.2tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.OS SummaryPage 91 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Maximum emission rate frompreconstruction permit. TSP <= 0.0063lb/hr. [N.J.A.C. 7:27-22.16(e)]None.None.None.6PM-10 (Total) <= 0.0063 lb/hr Maximumemission rate from operating permitapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.7FUGITIVE ASH EMISSIONS -The facilitymust not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), exceptduring periods of startup, shutdown, andmalfunction and as provided below.Startup, shutdown, and malfunctionexception is specified by 40 CFR62.14109(b) and 40 CFR 60.58b(a)(1).- The emission limit specified above doesnot cover visible emissions dischargedinside buildings or enclosures of ashconveying systems; however, the emissionlimit specified above does cover visibleemissions discharged to the atmospherefrom buildings or enclosures of ashconveying systems.- The provisions specified above do notapply during maintenance and repair of ashconveying systems. 40 CFR 60.39b(d)& [40CFR 62.14106(a)]Monitored by visual determination annually,based on the average of three tests.Compliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. This isbased on the requirement at 40 CFR60.58b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14106(a)]Other: Maintain records of annual method22 results along with all supportingcalculations. This is as specified at 40 CFR60.59b(d)(9). [40 CFR 60.39b(d)]&[40CFR 62.14109(a)].None.Page 92 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8The control devices CD1017 & CD1018shall comply with the design specified in thecontrol device details section of theapplication for operating permit [fromrenewal application BOP080001)Number of bags - 9Bag size - 7.2 ft2Total Bag Area - 65 FT2Bag Fabric - Polyester feltFabric Weave - non-wovenMaximum Air Flow/Cloth Area: 5.2 to 1Method of Bag Cleaning - pulse jetPressure drop across bag: 3 - 6 inches w.c.Design efficiency: 99.8 % [N.J.A.C.7:27-22.16(a)]None.None.None.9The control device CD1019 shall complywith the design specified in the controldevice details section of the application foroperating permit [from renewal applicationBOP080001)Number of bags - 36Bag size - 10.6 ft2Total Bag Area - 382 FT2Bag Fabric - PolypropyleneFabric Weave - feltMaximum Air Flow/Cloth Area: 5.24 to 1Method of Bag Cleaning - pulse jetPressure drop across bag: 3 - 6 inches w.c.Design efficiency: 99% [N.J.A.C.7:27-22.16(a)]None.None.None.Page 93 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Emission Unit:U16 Abrasive Blaster (E19) controlled by filter CD1021Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The permittee shall not use the equipment ina manner which will cause visible emissions,exclusive of condensed water vapor.[N.J.A.C. 7:27-22.16(e)]Monitored by visual determination eachmonth during operation, based on aninstantaneous determination. The permitteeshall conduct visual opacity inspectionsduring daylight hours. Visual inspectionsshall consist of a visual survey to identify ifthe stack has visible emissions, (other thancondensed water vapor), greater than theprescribed standard. If visible emissions areobserved, the permittee shall (1) Verify thatthe equipment and/or control device causingthe emission is operating according tomanufacturer's specifications and theoperating permit compliance plan. If theequipment or control device is not operatingproperly, the permittee shall take correctiveaction immediately to eliminate the excessemissions and 2) If the corrective actiontaken does not correct the opacity problemwithin 24 hours, the applicant shall performa check via a certified opacity reader, inaccordance with N.J.A.C. 7:27B-2. Such atest shall be conducted onceeach day untilcorrective action is taken to successfullycorrect the opacity problem. [N.J.A.C.7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage each monthduring operation , or manually in apermanently bound logbook. The permitteemust retain the following records: (1) Dateand time of inspection; (2) Emission pointnumber; (3) Operational status ofequipment; (4) Observed results andconclusions; (5) Description of correctiveaction taken if needed; (6) Date and timeopacity problem was solved, if applicable;(7) N.J.A.C. 7:27B-2 results, if conducted,and (8) Name of person(s) conductinginspection. [N.J.A.C. 7:27-22.16(e)]Other (provide description): Uponoccurrence of event the permittee mustreport any continuing permit violation to NJDEP pursuant to N.J.A.C. 7:27-22.19.[N.J.A.C. 7:27-22.19]2All particulate emissions from this emissionunit shall be exhausted through a dustcollector (CD1021). [N.J.A.C.7:27-22.16(a)]None.None.None.3The owner or operator shall inspect andmaintain the dust collector and replace thefilter media on a schedule necessary toachieve the required particulate controleffeciency as specified by the manufacturer.[N.J.A.C. 7:27-22.16(a)]Monitored by visual determination onceevery 2 weeks. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event , or manually in apermanently bound logbook. Recordeachinspection and maintenance event. [N.J.A.C.7:27-22.16(o)]None.OS SummaryPage 94 of 95New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 9/1/2009COVANTA ESSEX CO (07736)BOP090001Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4The control device CD1021 shall complywith the design specified in the controldevice details section of the application foroperating permit [from renewal applicationBOP080001)Number of bags - ??Bag size - ?? ft2Total Bag Area - ?? ft2Bag Fabric - PolyesterFabric Weave - feltFabric finish: plainMaximum Air Flow/Cloth Area: 1 to 1Method of Bag Cleaning - pulse jetPressure drop across bag: 4 - 6 inches w.c.Design efficiency: 99% [N.J.A.C.7:27-22.16(a)]None.None.None.Page 95 of 95

# COVANTA ESSEX CO (07736) Date: 9/1/2009



# BOP090001



# New Jersey Department of Environmental Protection

Facility Profile (General)

Municipal Waste Combustion using

mass-burn waterwall furnace and boiler that

generates electricity 4953

4939 State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC: Essex Mailing

Address: Street

Address: 183 RAYMOND BLVD

NEWARK, NJ 07105-4798

183 RAYMOND BLVD

NEWARK, NJ 07105-4798 Facility Name (AIMS): COVANTA ESSEX CO Facility ID (AIMS): 07736

NAICS:

Page 1 of 2

# COVANTA ESSEX CO (07736) Date: 9/1/2009



# BOP090001



# New Jersey Department of Environmental Protection

Facility Profile (General)

( ) - x

( ) - x

gkimiecik@covantaenergy.com Covanta Essex Company

George Kimiecik

Environmental Engineer

(973) 817-7322 x 183 Raymond Blvd

Newark, NJ 07105-4798 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Corporation

NJ EIN: 75611300000 Contact Type: BOP - Operating Permits

(973) 344-4999 x

( ) - x Covanta Essex Company

Richard R. Giordano

Plant Manager

(973) 344-0900 x 183 Raymond Boulevard

Newark, NJ 07105-4798 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Corporation

NJ EIN: 75611300000 Contact Type: On-Site Manager

(973) 344-4999 x

( ) - x Covanta Essex Company

Richard R. Giordano

Plant Manager

(973) 344-0900 x 183 Raymond Boulevard

Newark, NJ 07105-4798 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Corporation

NJ EIN: 75611300000 Contact Type: Responsible Official

Page 2 of 2

# COVANTA ESSEX CO (07736)

BOP090001



# New Jersey Department of Environmental Protection

Reason for Application Date: 9/1/2009



# Permit Being Modified

Permit Class: BOP Number: 80001

Description

of Modifications: This modification revised the following:

1. As required by U1-OS0 Ref.#6 of the current Operating Permit (OP), U1, OS1, Ref #17,

PM10 limit is now 22.8 pounds per hour based on stack test results and OS Summary, Ref

#41 is 299 tpy [Ref #6 has been removed from the OP.];

2. U1-OS0 Ref. #16 to refer to subpart Cb, which exempts these units from being subject to

subpart Db (Also, deleted Ref #96);

3. U1-OS1/OS3/OS5 & OS7/OS8/OS9 Ref.#39 to change the minimum reagent

concentration to 19% based on previous NJDEP approval which allowed the facility to be

exempt from the Risk Management Program, and

4. The Department re-stated requirements at U1, OS Summary, Refs #98-106 to reflect new

lower limits from 40 CFR 60 Subpart Cb, effective April 28, 2009.

5. At U1, OS Summary, Ref #71, updated Mercury emissions at the exit of the control

device to "shall not exceed 15 percent (from N.J.A.C. 7:27-27.4(a)(2)(ii) after January 3,

2006)." Updated the verbiage and citations from N.J.A.C. 7:27-27, revised September 5,

2006.

Page 1 of 1COVANTA ESSEX CO (07736)BOP090001New Jersey Department of Environmental ProtectionNon-Source Fugitive EmissionsDate:09/01/2009Total0.0000.0000.0000.0000.0000.0000.0000.000000000.000Page 1 of 1COVANTA ESSEX CO (07736)BOP090001New Jersey Department of Environmental ProtectionInsignificant Source Emissions9/1/2009Date:ISNJIDSource/GroupDescriptionEquipment TypeLocationDescriptionEstimate of Emissions (tpy)VOC(Total)NOxCOSOTSPPM-10PbHAPS(Total)Other(Total)IS1No. 2 Fuel Oil Tanks(<10,000 GallonsCapacity)Storage VesselIS2Fuel Oil Tank(>10,000 GallonsCapacity)Storage VesselTotal0.0000.0000.0000.0000.0000.0000.0000.000000000.000Page 1 of 1Equip.NJIDFacility'sDesignationEquipmentDescriptionEquipment TypeCertificateNumberInstallDateGrandFatheredLast Mod.(Since 1968)Equip.Set IDNew Jersey Department of Environmental ProtectionEquipment InventoryBOP090001COVANTA ESSEX CO (07736)9/1/2009Date:E11IPCP96000511/3/1990No7/29/1997MSW Boiler #1IncineratorE22IPCP96000511/26/1990No7/29/1997MSW Boiler #2IncineratorE33IPCP96000512/17/1990No7/29/1997MSW Boiler #3IncineratorE44SPCP96000111/1/1990NoLime Silo AStorage VesselE55SPCP96000211/1/1990NoLime Silo BStorage VesselE66SPCP96000311/1/1990NoLime Silo CStorage VesselE77EPCP96000611/1/1990NoDiesel GeneratorEmergency GeneratorE88EPCP96000711/1/1990NoDiesel Fire PumpEmergency GeneratorE99MPCP96001011/11/1991NoLime Slaker Vent AManufacturing andMaterials HandlingEquipmentE1010MPCP96001311/11/1991NoLime Slaker Vent BManufacturing andMaterials HandlingEquipmentE1212MPCP96001211/11/1991NoFlyash Silo 1Manufacturing andMaterials HandlingEquipmentE1313MPCP96001211/11/1991NoFlyash Silo 2Manufacturing andMaterials HandlingEquipmentE1414SPCP96000512/1/1995NoCarbon SiloStorage VesselE1616MPCP96000911/1/1990No11/1/1994Ash Conveyance Line "A" -CV500A & 502AManufacturing andMaterials HandlingEquipmentPage 1 of 2Equip.NJIDFacility'sDesignationEquipmentDescriptionEquipment TypeCertificateNumberInstallDateGrandFatheredLast Mod.(Since 1968)Equip.Set IDNew Jersey Department of Environmental ProtectionEquipment InventoryBOP090001COVANTA ESSEX CO (07736)9/1/2009Date:E1717MPCP96000911/1/1990No11/1/1994Ash Conveyance Line "B" -CV500B & 502BManufacturing andMaterials HandlingEquipmentE1818MPCP96000910/1/1994No10/1/1994Ferrous Belt Conveyor - CV610Manufacturing andMaterials HandlingEquipmentE1919GGEN0100013/6/2001NoAbrasive BlasterGP-Abrasive BlastingPage 2 of 2COVANTA ESSEX CO (07736)Date:9/1/2009New Jersey Department of Environmental ProtectionControl Device InventoryCDNJIDFacility'sDesignationDescriptionCD TypeInstallDateGrandFatheredLast Mod.(Since 1968)CDSet IDBOP090001CD1001Acid Gas Scrubber - Boiler #111/1/1990No1001Scrubber (Other)CD1002Acid Gas Scrubber - Boiler #211/1/1990No1002Scrubber (Other)CD1003Acid Gas Scrubber - Boiler #311/1/1990No1003Scrubber (Other)CD1004Electrostatic Precipitator - Boiler#111/1/1990No1004Electrostatic PrecipitatorCD1005Electrostatic Precipitator - Boiler#211/1/1990No1005Electrostatic PrecipitatorCD1006Electrostatic Precipitator - Boiler#311/1/1990No1006Electrostatic PrecipitatorCD1007Thermal DeNOx - Boiler #111/1/1994No7/29/19971007Selective Non-CatalyticReductionCD1008Thermal DeNOx - Boiler #211/1/1994No7/29/19971008Selective Non-CatalyticReductionCD1009Thermal DeNOx - Boiler #311/1/1994No7/29/19971009Selective Non-CatalyticReductionCD1010Carbon Injection for MercuryControl - Boiler #112/1/1995No6/21/19961010AdsorberCD1011Carbon Injection for MercuryControl - Boiler #212/1/1995No6/21/19961011AdsorberCD1012Carbon Injection for MercuryControl - Boiler #312/1/1995No6/21/19961012AdsorberCD1013Lime Silo A Baghouse11/1/1990No1013Particulate Filter(Baghouse)CD1014Lime Silo B Baghouse11/1/1990No1014Particulate Filter(Baghouse)CD1015Lime Silo C Baghouse11/1/1990No1015Particulate Filter(Baghouse)CD1017Flyash Silo A Baghouse11/11/1991No1017Particulate Filter(Baghouse)Page 1 of 2COVANTA ESSEX CO (07736)Date:9/1/2009New Jersey Department of Environmental ProtectionControl Device InventoryCDNJIDFacility'sDesignationDescriptionCD TypeInstallDateGrandFatheredLast Mod.(Since 1968)CDSet IDBOP090001CD1018Flyash Silo B Baghouse11/11/1991No1018Particulate Filter(Baghouse)CD1019Flyash Building Baghose11/11/1991No1019Particulate Filter(Baghouse)CD1020Carbon Silo Baghouse12/1/1995No1020Particulate Filter(Baghouse)CD1021Blaster Particulate Filter3/6/2001No1021Particulate Filter (Other)Page 2 of 2COVANTA ESSEX CO (07736)Date:9/1/2009New Jersey Department of Environmental ProtectionEmission Points InventoryPTNJIDFacility'sDesignationDescriptionConfig.Equiv.Diam.(in.)Height(ft.)Dist. toProp.Line (ft)Exhaust Temp. (deg. F)Exhaust Vol. (acfm)Avg.Min.Max.Avg.Min.Max.DischargeDirectionPTSet IDBOP090001PT1U0001MSW BOILER #1Round91279230285.0200.0300.0UpR220,000.0181,000.0140,000.0PT2U0002MSW BOILER #2Round91279230285.0200.0300.0UpR220,000.0181,000.0140,000.0PT3U0003MSW BOILER #3Round91279230285.0200.0300.0UpR220,000.0181,000.0140,000.0PT4U0006LIME SILO ARectangle127237560.0-10.0100.0HorizontalR1,176.01,176.01,176.0PT5U0007LIME SILO BRectangle127237560.0-10.0100.0HorizontalR1,176.01,176.01,176.0PT6U0008LIME SILO CRectangle127237560.0-10.0100.0HorizontalR1,176.01,176.01,176.0PT7U0013DIESEL GENERATORRound1243360915.0915.0915.0HorizontalR6,915.06,915.06,915.0PT8U0014DIESEL FIRE PUMPRound839125983.0982.0982.0HorizontalR1,200.01,200.01,200.0PT9U0009LIME SLAKER VENT ARound62025085.060.0140.0HorizontalR37.037.037.0PT10U0010LIME SLAKER VENT BRound62025085.060.0140.0HorizontalR37.037.037.0PT12U0012FLY ASH CONDITIONINGROOMRectangle87137680.040.0110.0HorizontalR2,000.02,000.02,000.0PT13U0004#2 FUEL OIL STORAGETANKRound3310060.0-10.0100.0DownR8.05.01.0PT14U0011CARBON SILORound123537560.0-10.0100.0HorizontalR1,200.01,200.0100.0PT15U0015ASH CONVEYANCESquare123537660.040.090.0HorizontalS96,000.06,000.00.0PT16U0016ABRASIVE BLASTERPage 1 of 1New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 1 MWC #1, 2, 3 Municipal Waste Combustors (E1, E2 & E3) - Subject to NSPS Subparts Cb and 40 CFR 62 Subpart FFFUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1MWC 1Operation of MWC # 1 atMaximum Input (423MMBtu/hr)Normal - SteadyStateE1CD1001 (T)CD1004 (T)CD1007 (P)CD1010 (S)PT15-03-001-120.08,760.0140,000.0220,000.0200.0300.0OS2MWC 1Operation of MWC # 1under MalfunctionconditionsMalfunctionE1CD1001 (T)CD1007 (P)CD1010 (S)PT15-03-001-120.0175.0140,000.0220,000.0200.0300.0OS3MWC 2Operation of MWC # 2 atMaximum Input (423MMBtu/hr)Normal - SteadyStateE2CD1002 (T)CD1005 (T)CD1008 (P)CD1011 (S)PT25-03-001-120.08,760.0140,000.0220,000.0200.0300.0OS4MWC 2Operation of MWC # 2under MalfunctionconditionsMalfunctionE2CD1002 (T)CD1008 (P)CD1011 (S)PT25-03-001-120.0175.0140,000.0220,000.0200.0300.0OS5MWC 3Operation of MWC # 3 atMaximum Input (423MMBtu/hr)Normal - SteadyStateE3CD1003 (T)CD1006 (T)CD1009 (P)CD1012 (S)PT35-03-001-120.08,760.0140,000.0220,000.0200.0300.0OS6MWC 3Operation of MWC # 3under MalfunctionconditionsMalfunctionE3CD1003 (T)CD1009 (P)CD1012 (S)PT35-03-001-120.0175.0140,000.0220,000.0200.0300.0OS7MWC 1Operation of MWC # 1 atMaximum Input (423MMBtu/hr) using CovantaLow-NOx (LN) ControlNormal - SteadyStateE1CD1001 (T)CD1007 (P)CD1010 (S)PT15-03-001-120.08,760.0140,000.0220,000.0200.0300.0Page 1 of 7New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 1 MWC #1, 2, 3 Municipal Waste Combustors (E1, E2 & E3) - Subject to NSPS Subparts Cb and 40 CFR 62 Subpart FFFUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS8MWC 2Operation of MWC # 2 atMaximum Input (423MMBtu/hr) using CovantaLow-NOx (LN) ControlNormal - SteadyStateE2CD1002 (T)CD1005 (T)CD1008 (P)CD1011 (S)PT25-03-001-120.08,760.0140,000.0220,000.0200.0300.0OS9MWC 3Operation of MWC # 3 atMaximum Input (423MMBtu/hr) using CovantaLow-NOx (LN) ControlNormal - SteadyStateE3CD1003 (T)CD1006 (T)CD1009 (P)CD1012 (S)PT35-03-001-120.08,760.0140,000.0220,000.0200.0300.0U 6 Lime Silo A Lime Storage Silo A (E4) controlled by filter CD1013UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Silo ASilo ANormal - SteadyStateE4CD1013 (P)PT42,920.08,760.01,176.01,176.0-10.0110.0Page 2 of 7New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 7 Lime Silo B Lime Storage Silo B (E5) controlled by filter CD1014UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS7Silo BSilo BNormal - SteadyStateE5CD1014 (P)PT52,920.08,760.01,176.01,176.0-10.0110.0U 8 Lime Silo C Lime Storage Silo C (E6) controlled by filter CD1015UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS8OS 008Lime Storage Silo - CNormal - SteadyStateE6CD1015 (P)PT62,920.08,760.01,176.01,176.0-10.0110.0Page 3 of 7New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 9 Slaker A Lime Slaker Vent A (E9)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS9Slaker ALime Slaker Vent ANormal - SteadyStateE9PT94,380.08,760.037.037.060.0140.0U 10 Slaker B Lime Slaker Vent B (E10)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS10Slaker BLime Slaker Vent BNormal - SteadyStateE10PT104,380.08,760.037.037.060.0140.0Page 4 of 7New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 11 Carbon Silo Activated Carbon Storage Silo (E14) controlled by filter CD1020UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS11Carbon SiloActivated Carbon StorageSilo controlled by filterCD1020Normal - SteadyStateE14CD1020 (P)PT148,760.08,760.01,200.01,200.0-10.0110.0U 12 Flyash Cond Flyash Conditioning Room (E12, E13) controlled by filters CD1017, 1018 & 1019UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS12Silo 1Flyash Storage in Silo 1(E12) controlled by filterCD1017Normal - SteadyStateE12CD1017 (P)CD1019 (S)PT128,760.08,760.02,000.02,000.040.0110.0OS15Silo 2Flyash Storage in Silo 2(E13) controlled by filterCD1018Normal - SteadyStateE13CD1018 (P)CD1019 (S)PT128,760.08,760.02,000.02,000.040.0110.0Page 5 of 7New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 13 Em Generator 7.4 MMBtu/hr Diesel Engine-driven Emergency Generator (E7)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS13GeneratorEmergency DieslGeneratorStandbyE7PT7250.0250.06,915.06,915.0915.0915.0U 14 Em FW Pump 1.59 MMBtu/hr Diesel Engine-driven Emergency Fire Pump (E8)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS14Fire PumpEmergency Diesel FirePumpStandbyE8PT8250.0250.01,200.01,200.0982.0982.0U 15 Ash Convey Ash Conveyance System (E16, E17, E18) controlled by filters CD1017, 1018 & 1019UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS16Ash Convey AAsh conveyance line Acontrolled by filterCD1017Normal - SteadyStateE16CD1017 (P)CD1019 (S)PT154,380.08,760.00.09,600.040.0110.0Page 6 of 7New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryCOVANTA ESSEX CO (07736)BOP090001Date:9/1/2009U 15 Ash Convey Ash Conveyance System (E16, E17, E18) controlled by filters CD1017, 1018 & 1019UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS17Ash Convey BAsh conveyance line Bcontrolled by filterCD1018Normal - SteadyStateE17CD1018 (P)CD1019 (S)PT154,380.08,760.00.09,600.040.0110.0OS18Ferrous SysFerrous Handling SystemNormal - SteadyStateE18CD1019 (P)PT154,380.08,760.00.09,600.040.0110.0U 16 Abrasive Bla Abrasive Blaster (E19) controlled by filter CD1021UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1OS 019Blast Cleaning controlledby filter CD1021Normal - SteadyStateE19CD1021 (P)PT16Page 7 of 7Date:9/1/2009New Jersey Department of Environmental ProtectionSubject Item Group InventoryGR1 NSPS Sub AGroup NJID:Members:TypeIDOSStepUU 1OS0 SummaryUU 15OS0 SummaryFormal Reason(s) for Group/Cap:9OtherOther (explain):Showing Subpart A requirements applicable to 2 emission units (U1 & U15)Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group:Operating Circumstances:Page 1 of 1