Process Information

1 Name of legal owner of facility:

Gulf Power Company

2 Name of legal operator of facility, if different from legal owner:

Gulf Power Company

3 Address of ___ legal owner or ____ operator:

One Energy Place

Pensacola, FL 32520 - 0100

4a Plant Name (as reported on U.S. DOE/EIA Form-860 (2007), "Annual Electric Generator Report", schedule 2, line 1, page 37, question 1)

OR Plant Name (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report", schedule 2, page 1, question 1):

Crist

4b EIA Plant Code (as reported on U.S. DOE/EIA Form-860 (2007), schedule 2, line 1, page 37, question 2) OR Plant ID (as reported on U.S. 

DOE/EIA Form EIA-923 (2008), schedule 2, page 1, question 2):

641

5 Complete street address of facility (physical location):

11999 Pate Street

Pensacola, FL 32514

6 Provide mailing address if different:

One Energy Place

Pensacola, FL 32520 - 0340

7 Name and title of contact(s) able to answer technical questions about the completed survey:

Sarah Markham, Engineer II

8 Contact(s) telephone number(s):

(205) 257-6780

and e-mail address(es):

sasander@southernco.com

9 Is this facility considered to be owned or operated by a small entity as defined by the Regulatory Flexibility Act? 

____ Yes _X__ No ____ Don't know

10 Which of the following fossil fuels or other material(s) are fired in any steam generating unit at this facility?

__X_ coal __X__ oil (including pet coke) _X__ natural gas

__X_ other (specify in question 14 below)

11 Which of the following fossil fuel or other material(s) are permitted1

 to be fired in any steam generating unit at this facility?

_X__ coal _X_ oil (including pet coke) _X__ natural gas

_X__ other (specify in question 14 below)

12 If coal or solid fuel, as described below, derived from a fossil source is fired, indicate which rank of coal or solid fuel was utilized

during the previous 12 months prior to the receipt of this ICR:2,3

____ lignite (% _____) ____ subbituminous (% _____)

_X__ bituminous (% _100_) ____ anthracite (% _____)

____ coal refuse (including gob, culm, and subbituminous-derived coal refuse) (% _____)

____ synfuel (including, but not limited to, briquettes, pellets, or extrusions which are formed by binding materials, or processes

 that recycle materials) (%_____)

 (please specify the type or form of synfuel used ___________________________________________)

____ petroleum coke (% _____)

13 If oil is fired, indicate which type of oil was utilized during the previous 12 months prior to the receipt of this ICR:4

_X__ distillate (% _91.3_)

_X__ other (specify on spec used oil_) (% _8.7_)
____ residual or bunker C (% _____)

14a If "other" was checked in questions 10 or 11 above indicating that any non-fossil fuel or other material (including, but not limited to, 

plastics, treated wood, rubber belting or gaskets, whole tires, tire-derived fuel, boiler cleaning solutions, animal wastes, etc.) is 

either utilized or permitted to be used, please indicate below what materials are combusted in the boiler and in what quantities

(specify whether this quantity is on a weight percentage or heat [Btu] basis). Also indicate (yes/no) whether you are permitted5 to 

burn non-fossil fuel(s) or other material(s) even if you do not actually burn them.

14b If "other" was checked in questions 10 or 11 above indicating that any non-fossil fuel or other material (including, but not limited to,

plastics, treated wood, rubber belting or gaskets, whole tires, tire-derived fuel, boiler cleaning solutions, animal wastes, etc.) is 

either utilized or permitted to be used, were such material to be classified as "solid waste" under the Resource Conservation and 

Recovery Act and, thus make the utilizing unit subject to CAA section 129, would you continue to utilize (i.e., use as a fuel) the 

material? ____ Yes ____ No _X__ Neither

Explain: Until the regulations are finalized, we cannot determine with certainty whether we would use these other materials or not.

1

 "Permitted" in this context, refers to the fuels that the permit anticipates will be combusted at the facility.

2

 If the boiler is fired by a blend of coal ranks, please specify percentage (separately, on both a mass and on a Btu basis) of each coal rank

(e.g., 85% subbituminuous/15% bituminous).

3

 In reference to footnote 1, if necessary, a notation can be added to a utilized fuel type that is not listed in the operating permit noting 

the reason the fuel type was combusted (e.g., "the permitting agency allowed this fuel to be combusted for special testing and research

purposes").

4

 If the boiler is fired by a blend of fuel oil ranks, please specify percentage (separately, on both a volume and on a Btu basis) of each

fuel oil rank (e.g., 85% residual oil/15% distillate).

5

 If necessary, a notation can be added to a utilized fuel type that is not listed in the operating permit noting the reason the fuel was

combusted (e.g., "the permitting agency allowed this fuel to be combusted for special testing and research purposes").

1,348,956 gallons burned in 2009

Quantity/year

No Biomass Fuel was burned in 

either Unit 4 or 5 in 2009

15,054 gallons burned in 2009

No Oil Contaminated Soil was 

burned in 2009.

Other Material

Biomass in Units 4 & 5 

On Specification Used Oil which 

meets 40 CFR 279 and less than 50 

ppm PCB for energy recovery 

purposes.

Boiler cleaning wastes that are not 

hazardous as defined in 40 CFR Part 

261, Subpart B.

On Site Generated Oil Contaminated 

Soil which meets 40 CFR 279 and less 

than 50 PCB for energy recovery 

purposes.

Actually burn

No

Yes

Yes

No

Permitted to burn

Yes; untreated materials: wood chips at 

4.7 tons/hr, switch grass at 2.9 tons/hr, 

sawdust at 3.7 tons/hr, sander dust at 3.7 

tons/hr and shall not exceed 40.2 MMBtu 

per hour for each unit. Only one 

carbonaceous fuel type may be fired at a 

time. 

Yes; Crist 4-7 are permitted to burn at 

each unit's permitted heat input for oil 

but not to exceed 50,000 gallons/yr per 

unit

Yes; Crist 4-7 are permitted to burn non 

hazardous boiler cleaning wastes not to 

exceed 50 gallons per minute.

Yes; Crist 4-7 are permitted to burn at 

each unit's permitted heat input for oil 

but not to exceed 50,000 gallons/yr per 

unit
15 Identification (or designation) of all coal- and oil-fired steam generating units (boilers) (as defined by Clean Air Act section 112(a)(8))

located at this facility. Boiler ID

6

coal rank or type of oil) 

Original design fuel (i.e., 

r

Design heat input, 

(MMBtu/hr)7, q

Present maximum heat 

input, (MMBtu/hr)8,p

MWe Gross capacity

summer o

MWe Net Capacity

summer 

n

efficiency (%, HHV) 

Original design gross 

m

Present operating gross 

efficiency (%, HHV) 

l

Design steam pressure 

(psig) 

k

Operating steam pressure 

(psig) 

j

Design steam temperature 

(

oF) I 

Operating steam 

temperature (

oF) 

h

Design steam reheat 

temperature (

oF)9, g

Operating steam reheat 

temperature (

oF)10, f

Fuel11, e

Hours/year operated12, d

Average annual capacity 

factor for the past 3 years 

c

Applicable NSPS b Estimated year of 

retirement13, a

4 bituminous CBI CBI 82 78 89.4 N/A 1800 1760 1000 992 1000 992 bituminus coal, 

No. 2 fuel oil, 

natural gas, onspec used oil, 

biomass, boiler 

cleaning waste, 

CBI CBI none N/A

5 bituminous CBI CBI 82 78 89.4 N/A 1800 1765 1000 992 1000 990 bituminus coal, 

No. 2 fuel oil, 

natural gas, onspec used oil, 

biomass, boiler 

cleaning waste, 

CBI CBI none N/A

6 bituminous CBI CBI 320 302 89 87 2400 2346 1000 997 1000 1000 bituminus coal, 

No. 2 fuel oil, 

natural gas, onspec used oil, 

boiler cleaning 

waste, 

CBI CBI none N/A

7 bituminous CBI CBI 500 472 89 87.63 2400 2400 1000 997 1000 997 bituminus coal, 

No. 2 fuel oil, 

natural gas, onspec used oil, 

boiler cleaning 

waste, 

CBI CBI none N/A

Notes

"N/A" means not available.

a Gulf Power has not committed to actual retirement dates for Plant Crist. Gulf Power continually evaluates retirement scenarios with respect to its generating units for a variety of planning purposes, taking into account a wide range of variables. 

 While, the company assumes financial "retirement dates" for accounting purposes, for example, for depreciation schedules or for FERC or Public Service Commission uses, these dates are not indicative of the unit's 

 for accounting purposes, for example, for depreciation schedules or for FERC or Public Service Commission uses, these dates are not indicative of the unit's actual retirement date. 

b

 Where no NSPS is identified, the unit is not currently subject to any NSPS.

c CBI

d CBI

e

 Indicates the fuels burned in the previous calendar year (January to December 2009). .

f

 Represents the average reheat steam temperature when the unit operated at gross normal full load over a three year period (January 2007 to December 2009).

g

 Based on the thermal design of the unit as represented on the turbine heat balance sheet. 

h Represents the average steam temperature when the unit operated at gross normal full load over a three year period (January 2007 to December 2009). 

i

 Based on the thermal design of the unit as represented on the turbine heat balance sheet. 

j

 Represents the average throttle pressure when the unit operated at gross normal full load over a three year period (January 2007 to December 2009). 

k

 Based on the thermal design of the unit as represented on the turbine heat balance sheet. 

l

 Based on the most recent actual test of the boiler efficiency, unless no recent boiler efficiency test was available. Where no recent test was available, that status is indicated.

m

 Taken directly from the original contract boiler data sheet.

n

 Identifies the net normal full load as of May 2009; taken directly from the 2009 installed and authorized document. Gulf Power does not change unit capacities from season to season. 

o

 Identifies the gross normal full load as of May 2009. Gulf Power does not change unit capacities season from season.

p CBI

q CBI

r

 Based on the original contract boiler data sheet; only the primary fuel is listed if multiple fuels were included on the data sheet. See also text to previous

 response (Part I, No. 11), which indicates that the design fuel simply means the fuel for which the boiler is optimized to operate at maximum possible efficiency, 

 but that the boiler was designed to handle and burn a range of fuels. 

6

 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

7

 Per fuel burned in the boiler. Report this based on higher heating value (HHV).

8

 Per fuel burned in the boiler. Report this based on higher heating value (HHV).

9

 Please indicate if more than one steam reheat cycle is utilized, and, if so, please provide information for both.

10 Please indicate if more than one steam reheat cycle is utilized, and, if so, please provide information for both.

11 Indicate the fuels utilized for the indicated boiler, and percentages, as indicated in questions 11 - 13.

12 The "hours/year operated" would be the average of the actual number of hours the unit operated in 1 year based on the last 3 years of operation.

13 This can be treated as CBI and can be submitted through the proper CBI procedure if desired.
16 For each boiler noted in Part I, question 15, provide the following information for each current emission control device installed

and operating and/or planned (please designate the order of the emission controls - 1 for the first control following the boiler, 2

for the second control following the boiler, etc.):

Boiler ID14 Type15 NOx control16 SO2 control17 PM control18 Other control19

4 tangential - fired 1) low NOx burner tips (1998) 

2) SNCR (4/2006)

5) FGD (12/15/09) 3) hot side ESP (rebuilt in 

3/2008) 

4) Cold side ESP (01/1976)

N/A

5 tangential - fired 1) low NOx burner tips (1998) 

2) SNCR (4/2006)

5) FGD (12/15/09) 3) hot side ESP (rebuilt in 

3/2008) 

4) Cold side ESP (01/1976)

N/A

6 wall-fired 1) low NOx burner (11/2005) 

2) SNCR (11/2005) 5) SCR (2012)

4) FGD (12/15/09) 3) Cold side ESP (01/1994) N/A

7 wall-fired 1) low NOx burner (5/2004) 2) SCR (04/2005) 

- the SCR uses a titania-vanadia based ceramic 

catalyst and anhydrous ammonia as the 

reductant; the catalyst is not specifically 

designed to reduce SO3 formation 1 

4) calcium-based wet flue gas 

desulfurization (FGD) 

(12/15/09) 

3) Cold side ESP (04/2004) N/A

Note: "N/A" means not applicable.

1

 When making catalyst decisions, the primary goal is to achieve the desired NOx performance, with a secondary goal of minimizing SO3 formation. 

14 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

15 Examples: tangential-fired; cyclone; wall-fired; circulating fluidized bed (CFB)

16 Examples: low-NOx burners; selective catalytic reduction (SCR); selective non-catalytic reduction (SNCR); over-fire air (OFA). Include

specific date that control went online or planned operational date for new installation. If this boiler's control configuration utilizes a SCR,

please include the type of material from which the catalyst is manufactured and the type of reductant used in with the SCR (e.g., anhydrous

ammonia, urea, other). Also, please note if the catalyst is specifically designed to reduce SO3 formation?

17 Examples: wet flue gas desulfurization (FGD; any type); dry scrubbing (any type); specify whether calcium- or sodium-based. Include 

specific date that control went online or planned operational date for new installation. 

18 Examples: fabric filter; cold-side electrostatic precipitator (ESP); hot-side ESP; cyclone or multiclone; venturi scrubber. Include specific

date that control went online or planned operational date for new installation.

19 Please indicate systems installed specifically to control any other pollutants (e.g., Hg, SO3, etc.). Examples: activated carbon injection (ACI);

Powerspan ECO®; dry sorbent injection or wet ESP for SO3 control; flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other);

additive use for mercury control (e.g., bromine; scrubber additives). Include specific date that control went online or planned operational date for 

new installation. Also include any pollutants controlled by this technology (e.g., control technology [pollutant controlled]).
17 For each boiler noted in Part I, question 15, provide the company (prime vendor) name and company contact information for each

HAP-specific (e.g., mercury, hydrogen chloride) control technology that you have either contracted for, are installing, or have installed

for the purpose of participating in a control technology demonstration project20 (e.g., U.S. Department of Energy program, consent decree,

etc.).

Name Telephone Address

4 N/A N/A N/A N/A

5 N/A N/A N/A N/A

6 N/A N/A N/A N/A

7 N/A N/A N/A N/A

Note: "N/A" means not applicable.

20 A control technology demonstration project is defined as a U.S. Government (e.g., U.S. Department of Energy program) sponsored

(in whole or in part) project or mandate (e.g., as a result of a consent decree) that adds a HAP control technology to a facility's unit to

demonstrate the technology's HAP removal performance.

21 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

Company (vendor) contact information Boiler ID21 Company (vendor) name
18 For the control technologies identified in Part I, question 17, provide the date of actual start-up of the demonstration (if the control

is currently operating), the date of expected or projected start-up, the date the demonstration was completed, the type of HAP

control installed (e.g., sorbent and type; pre-combustion boiler chemical additive; combustion boiler chemical additive), the desired

HAP emission reduction or rate (if any), and the coal rank(s) upon which the demonstration was conducted. Please specify the format 

of the target HAP emission reduction rate (e.g., lb/MWh, lb/TBtu, percent reduction, etc.). If the format of the target end-point is

percent reduction, provide (1) an estimate of what an equivalent emission rate would be (and specify the format of the equivalent

emission rate), and (2) the basis for calculating the percent reduction (i.e., where the "inlet" and "outlet" are).

Boiler ID22

Demonstration 

activity actual startup date

Demonstration 

activity projected 

start-up date

Demonstration 

activity end-date or 

projected end-date

Type of control (e.g., 

sorbent and type; 

chemical additive23)

Desired HAP emission 

reduction (%) or 

emission rate

Coal rank(s) in use

4 N/A N/A N/A N/A N/A N/A

5 N/A N/A N/A N/A N/A N/A

6 N/A N/A N/A N/A N/A N/A

7 N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

22 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

23 If additive is used, please indicate injection point.
19 For each boiler noted in Part I, question 15, provide the company (prime vendor) name and company contact information for each

HAP (e.g., mercury, hydrogen chloride, etc.) control technology that you have either contracted for, are installing, or have installed

for the purpose of provide a non-demonstration, full-scale operating system.

Name Telephone Address

4 N/A N/A N/A N/A

5 N/A N/A N/A N/A

6 N/A N/A N/A N/A

7 N/A N/A N/A N/A

Note: "N/A" means not applicable.

24 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

Company (vendor) contact information

Boiler ID24 Company (vendor) name
20 For the control technologies identified in Part I, question 19, provide the date of actual start-up (if the control is currently operating), the

date of expected or projected start-up, the type of HAP control installed (e.g., sorbent and type; pre-construction boiler chemical additive;

combustion of boiler chemical additive), the guaranteed HAP emission reduction or emission rate, the sorbent feed rate upon which the 

guarantee is based, and the coal rank(s) upon which the guarantee is based. Please specify the format of the guarantee (e.g., lb/MWh,

lb/TBtu, percent reduction, etc.). If the format of the guarantee is percent reduction, provide (1) an estimate of what an equivalent emission

rate would be (and specify the format of the equivalent emission rate), and (2) the basis for calculating the percent reduction (i.e., where the

"inlet" and "outlet" are).

Boiler ID25 Actual start-up date Expected or projected 

start-up date

Type of control (e.g., 

sorbent and type; 

chemical additive)26

Guaranteed HAP 

emission reduction 

(%) or emission rate

Sorbent or additive 

feed rate on which 

guarantee is based

Coal rank(s) upon 

which guarantee is 

based

4 N/A N/A N/A N/A N/A N/A

5 N/A N/A N/A N/A N/A N/A

6 N/A N/A N/A N/A N/A N/A

7 N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

25 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

26 If additive is used, please indicate injection point.
21 For each boiler noted in Part I, question 15, provide the following information:

PM28 PM10

(29) PM2.5(30) SO2 HCl and/or 

HF

HCN

Metal 

HAP31 Hg CO

Other 

organics 

(specify)

Other pollutant (specify)

4 Steady-State 0.10 lb/mmbtu 

Soot-blow 0.30 lb/mmbtu 

Title V permit; annual test 

Reference Method by 5 or 17

N/A N/A Solid or Liquid Fuel @ 2.4 lb/mmbtu; 24 - hr daily 

average; Liquid Fuel S% content not greater than 

2.18% S by weight; #2 Oil or On-spec Used Oil not to 

exceed 0.5% S by weight. (Title V Permit); 

Future FGD limit @ 886 tons/30 operational day. (Air 

Construction Permit)

N/A N/A N/A N/A N/A N/A Facility Wide NOx Limit of 

0.20 lb/mmbtu (30 day 

average applicable only 

when Unit 7 SCR is on-line.) 

5 Steady-State 0.10 lb/mmbtu 

Soot-blow 0.30 lb/mmbtu 

Title V permit; annual test 

Reference Method by 5 or 17

N/A N/A Solid or Liquid Fuel @ 2.4 lb/mmbtu; 24 - hr daily 

average; Liquid Fuel S% content not greater than 

2.18% S by weight; #2 Oil or On-spec Used Oil not to 

exceed 0.5% S by weight. (Title V Permit); 

Future FGD limit @ 886 tons/30 operational day. (Air 

Construction Permit)

N/A N/A N/A N/A N/A N/A Facility Wide NOx Limit of 

0.20 lb/mmbtu (30 day 

average applicable only 

when Unit 7 SCR is on-line.) 

6 Steady-State 0.10 lb/mmbtu 

Soot-blow 0.30 lb/mmbtu 

Title V permit; annual test 

Reference Method by 5 or 17

N/A N/A Solid or Liquid Fuel @ 2.4 lb/mmbtu; 24 - hr daily 

average; Liquid Fuel S% content not greater than 2.18 

% S by weight; #2 Oil or On-spec Used Oil not to 

exceed 0.5% S by weight. Unit 6 not to exceed 38,945 

tons/yr; (Title V Permit); Future 

FGD limit @ 886 tons/30 operational day. (Air 

Construction Permit)

N/A N/A N/A N/A N/A N/A Facility Wide NOx Limit of 

0.20 lb/mmbtu (30 day 

average applicable only 

when Unit 7 SCR is on-line.) 

7 Steady-State 0.10 lb/mmbtu 

Soot-blow 0.30 lb/mmbtu 

Title V permit; annual test 

Reference Method by 5 or 17

N/A N/A Solid or Liquid Fuel @ 2.4 lb/mmbtu; 24 - hr daily 

average; Liquid Fuel S% content not greater than 

2.18% S by weight; #2 Oil or On-spec Used Oil not to 

exceed 0.5% S by weight. (Title V Permit); 

Future FGD limit @ 886 tons/30 operational day. (Air 

Construction Permit)

N/A N/A N/A N/A N/A N/A Facility Wide NOx Limit of 

0.20 lb/mmbtu (30 day 

average applicable only 

when Unit 7 SCR is on-line.) 

Unit 7 Bypass NOx limit at 

0.35 lb/mmbtu (24 hr 

average)

Note: "N/A" means not applicable.

27 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

28 If the boiler has separate permitted emission limits for filterable and condensable PM, respectively, please indicate those separate limits. 

Also include the compliance test method utilized.

29 List the compliance test method utilized.

30 List the compliance test method utilized.

31 Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium;

indicate permit level for all metal HAP for which a permit level has been developed.

Permitted emission limit (indicate type of permit and format of emission limit)

Boiler ID27
22 For each boiler noted in Part I, question 15, provide the following information:

PM33 PM10 PM2.5 SO2 HCl and/or HF HCN Metal HAP34 Hg CO

Other organics 

(specify)

Other 

pollutant 

(specify)

4 HS-ESP: 99.1% collection efficiency 1 N/A N/A FGD: 98% instantaneous 

removal efficiency to meet a 

95% 30-day rolling average 

removal efficiency,7

N/A N/A N/A N/A N/A N/A N/A

4 CS-ESP: 99.2% collection efficiency 2

5 HS-ESP:99.1% collection efficiency 3 N/A N/A FGD: 98% instantaneous 

removal efficiency to meet a 

95% 30-day rolling average 

removal efficiency,7

N/A N/A N/A N/A N/A N/A N/A

5 CS-ESP: 99.2% collection efficiency 4

6 CS-ESP: 0.05 lb/MMBtu, filterable5 N/A N/A FGD: 98% instantaneous 

removal efficiency to meet a 

95% 30-day rolling average 

removal efficiency,7

N/A N/A N/A N/A N/A N/A N/A

7 CS-ESP: 0.05 lb/MMBtu, filterable6 N/A N/A FGD: 98% instantaneous 

removal efficiency to meet a 

95% 30-day rolling average 

removal efficiency,7

N/A N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

1

 Hot Side ESP guarantee expired 2008

2

 Cold Side ESP guarantee expired 1998

3

Hot Side ESP guarantee expired 2008

4

 Cold Side ESP guarantee expired 1995

5

 Cold Side ESP guarantee expired 1995

6

 Cold Side ESP guarantee expired 2004

7

 These values are not vendor guaranteed rates, but are the performance expectations for the FGD provided by our internal engineering group. 

 Like vendor guarantees, these performance expectations are dependent on specific operating conditions.

23 Was any other guarantee level sought or offered? __X__ Yes ____ No

Please elaborate.

Crist 4 & 5 Hot Side ESP in 2008

32 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

33 If the boiler has separate guaranteed emission rate for filterable and condensable PM, respectively, please indicate those separate emission rates.

34 Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, cobalt, lead, manganese, nickel, phosphorus, and selenium; 

indicate permit level for all metal HAP for which a permit level has been developed.

Most recent guaranteed emission rate for each pollutant for which there is a permitted emission limit

Boiler ID32
24 For each boiler noted in Part I, question15, provide the following information:

PM36 PM10 PM2.5 SO2

HCl 

and/or 

HF

HCN

Metal 

HAP37 Hg CO

Other 

organics 

(specify)

4 Particulate emission tests for steady state and soot blow are 

conducted annually. Results are required to be reported to 

FDEP within forty five days of completion of testing. FDEP 

must be notified at least 14 days in advance of all emission 

tests. Compliance Assurance Monitoring (CAM) reports for 

Particulate are reported on a semi-annual basis. All records 

must be maintained for 5 years."

N/A N/A Sulfur Dioxide emissions tests are conducted annually. 

Results are required to be reported to FDEP within forty five 

days of completion of testing. FDEP must be notified at least 

14 days in advance of all emission tests. Daily compliance is 

determined by fuel sampling or by continuous emission 

monitoring systems certified under 40 CFR Part 75. Excess 

Emissions are required on a quarterly basis to FDEP. All 

records must be maintained for 5 years. 

N/A N/A N/A N/A N/A N/A

5 Particulate emission tests for steady state and soot blow are 

conducted annually. Results are required to be reported to 

FDEP within forty five days of completion of testing. FDEP 

must be notified at least 14 days in advance of all emission 

tests. Compliance Assurance Monitoring (CAM) reports for 

Particulate are reported on a semi-annual basis. All records 

must be maintained for 5 years."

N/A N/A Sulfur Dioxide emissions tests are conducted annually. 

Results are required to be reported to FDEP within forty five 

days of completion of testing. FDEP must be notified at least 

14 days in advance of all emission tests. Daily compliance is 

determined by fuel sampling or by continuous emission 

monitoring systems certified under 40 CFR Part 75. Excess 

Emissions are required on a quarterly basis to FDEP. All 

records must be maintained for 5 years. 

N/A N/A N/A N/A N/A N/A

6 Particulate emission tests for steady state and soot blow are 

conducted annually. Results are required to be reported to 

FDEP within forty five days of completion of testing. FDEP 

must be notified at least 14 days in advance of all emission 

tests. Compliance Assurance Monitoring (CAM) reports for 

Particulate are reported on a semi-annual basis. All records 

must be maintained for 5 years."

N/A N/A Sulfur Dioxide emissions tests are conducted annually. 

Results are required to be reported to FDEP within forty five 

days of completion of testing. FDEP must be notified at least 

14 days in advance of all emission tests. Daily compliance is 

determined by fuel sampling or by continuous emission 

monitoring systems certified under 40 CFR Part 75. Excess 

Emissions are required on a quarterly basis to FDEP. All 

records must be maintained for 5 years. 

N/A N/A N/A N/A N/A N/A

7 Particulate emission tests for steady state and soot blow are 

conducted annually. Results are required to be reported to 

FDEP within forty five days of completion of testing. FDEP 

must be notified at least 14 days in advance of all emission 

tests. Compliance Assurance Monitoring (CAM) reports for 

Particulate are reported on a semi-annual basis. All records 

must be maintained for 5 years."

N/A N/A Sulfur Dioxide emissions tests are conducted annually. 

Results are required to be reported to FDEP within forty five 

days of completion of testing. FDEP must be notified at least 

14 days in advance of all emission tests. Daily compliance is 

determined by fuel sampling or by continuous emission 

monitoring systems certified under 40 CFR Part 75. Excess 

Emissions are required on a quarterly basis to FDEP. All 

records must be maintained for 5 years. 

N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

35 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

36 If the boiler's monitoring, recordkeeping, and reporting requirements require your company to monitoring, keep records, and report filterable

and condensable PM separately, please describe the separate actions required.

37 Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium;

indicate permit level for all metal HAP for which a permit level has been developed.

Required monitoring, recordkeeping, and reporting requirements for each pollutant for which there is a permitted emission limit

Boiler ID35
25 For the control technologies identified in Part I, questions 17 and 19, provide the cost information requested.38

Facility Name/Unit No.: N/A

Retrofit to existing boiler? 

Installation on a new boiler?

Total Capital Investment: $ -

Total Annual Operating and Maintenance Costs: $ - (Include base year for operating costs [e.g., 2006]

Note: "N/A" means not applicable.

26 Are any other means of emission control (for any pollutant) employed on any boiler noted in Part I, question 15 (e.g., low-ash coal,

coal or oil with low trace constituents, etc.)? Please specify.

Plant Crist currently utilizes a blend of coals to meet the plant SIP SO2 limits. 

38 This can be treated as CBI and can be submitted through the proper CBI procedure if desired.
Fuel Analysis39

1a Plant or facility name from Part I, question 4a: 

Crist

1b Plant or facility code from Part I, question 4b:

Plant Code - 641

39 The respondent should reply to this ICR with separate pages 18 through 24 (Part II) for each of their facilities.
2 For each individual coal and oil shipment received during the preceding 12 calendar months, provide the following information,

as available (indicated N/A if not available; use additional pages, as necessary):

D.B. D.B. D.B.

State/Country County42 Coal seam43 % Sulf % Ash Btu/lb

1,618 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.75 15.18 12,812

1,611 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.88 15.88 12,609

1,514 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.83 13.77 12,973

1,528 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.94 15.6 12,656

1,444 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1 15.29 12,803

1,502 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.87 16.2 12,662

1,617 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.93 15.89 12,701

1,614 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 14.95 12,776

1,589 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.91 15.3 12,788

1,487 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.98 16.17 12,694

1,441 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.98 16.26 12,608

1,508 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.8 16.38 12,655

1,481 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.93 14.9 12,867

1,499 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.94 14.15 12,994

1,626 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.91 14.78 12,771

1,464 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.88 14.63 12,760

1,511 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.83 14.89 12,822

1,445 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.85 15.94 12,668

1,424 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.86 14.84 12,819

1,472 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 14.77 12,827

1,426 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.96 14.35 12,851

1,429 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1 14.17 12,843

1,474 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.71 12.34 13,327

1,488 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.92 13.82 12,939

1,590 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.93 14.8 12,910

1,459 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.92 15.08 12,691

1,446 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1 14.37 12,952

1,546 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.9 14.87 12,859

1,382 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.88 14.27 12,929

1,516 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.93 15.01 12,483

1,506 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.96 15.94 12,363

1,535 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.95 15.38 12,607

1,529 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.98 15.05 12,714

1,476 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.91 14.99 12,702

1,437 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.07 15.32 12,670

1,494 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.01 14.98 12,668

1,498 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.85 14.9 12,838

1,475 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.03 15.41 12,817

1,528 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.87 15.28 12,642

1,479 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.92 14.49 12,843

1,474 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.03 14.88 12,614

1,372 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 15.03 12,791

1,512 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.8 15.39 12,691

1,559 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.88 15.26 12,689

1,401 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.96 14.89 12,742

1,444 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.18 15.61 12,627

1,536 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.88 14.35 12,846

1,511 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.89 14.85 12,760

1,623 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.85 15.64 12,655

1,427 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.82 14.63 12,866

1,426 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.82 15.14 12,876

1,466 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.98 14.41 12,889

1,407 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.76 12.04 13,361

1,441 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.99 13.2 13,076

1,494 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.97 13.94 12,903

1,521 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.72 15.24 12,802

1,385 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.82 15.57 12,755

Vendor Analyses

Amount received, dry Fuel source

basis, short tons40

ID # of boiler(s) firing 

fuel41

Fuel shipment 

method
D.B. D.B. D.B.

State/Country County42 Coal seam43 % Sulf % Ash Btu/lb

Vendor Analyses

Amount received, dry Fuel source

basis, short tons40

ID # of boiler(s) firing 

fuel41

Fuel shipment 

method

1,616 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.96 13.16 13,083

1,542 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.95 14.39 12,877

1,517 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.75 13.97 13,063

1,390 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.89 13.52 13,200

1,481 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.89 14.42 12,832

1,384 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.86 13.83 13,148

1,528 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.91 13.75 12,977

1,491 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.72 14.62 12,960

1,526 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.83 13.25 13,149

1,435 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.82 14.59 12,892

1,468 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.83 13.67 13,035

1,431 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.85 15.06 13,060

1,397 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.85 15.27 12,699

1,452 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.87 15.15 12,726

1,396 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.81 14.77 12,846

1,424 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 15.14 12,761

1,490 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.72 15.4 12,812

1,520 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.92 13.9 13,131

1,611 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.9 13.52 13,093

1,510 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.87 13.09 13,206

1,464 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 13.47 13,145

1,505 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.91 14.7 12,820

1,440 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.02 14.67 12,952

1,479 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.93 13.5 13,113

1,413 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.96 13.29 13,214

1,551 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.86 13.43 13,172

1,474 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.92 13.64 13,142

1,447 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.81 14.02 13,006

1,453 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.81 13.91 13,020

1,614 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.85 14.62 12,976

1,427 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.98 14.66 12,931

1,423 4, 5, 6, 7 WV BOONE STOCKTON BARGE 1.01 12.82 13,207

1,424 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.9 13.92 13,068

1,445 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.93 12.19 13,370

1,584 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 16.13 12,741

1,568 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.52 14.64 12,975

1,429 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.79 13.8 13,045

1,600 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.79 14.66 12,837

1,565 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.79 14.06 13,032

1,461 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.89 13.85 13,000

1,444 4, 5, 6, 7 WV BOONE STOCKTON BARGE 0.84 14.8 12,834

6,484 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.8 8.39 13,468

6,577 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.72 8.22 13,485

6,917 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.21 13,566

6,410 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.61 8.21 13,517

6,842 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.63 8.32 13,509

6,466 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.74 8.08 13,581

6,925 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.78 8.43 13,509

6,217 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.66 8.18 13,518

6,832 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.68 8.01 13,595

6,213 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.71 8.08 13,593

6,738 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.08 13,580

6,253 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.76 8.27 13,513

6,682 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.83 8.25 13,576

6,119 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.83 8.26 13,566

6,705 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.72 8.18 13,525

6,137 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.76 8.14 13,544

6,685 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.81 8.41 13,522

6,005 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.79 8.34 13,519
D.B. D.B. D.B.

State/Country County42 Coal seam43 % Sulf % Ash Btu/lb

Vendor Analyses

Amount received, dry Fuel source

basis, short tons40

ID # of boiler(s) firing 

fuel41

Fuel shipment 

method

6,830 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.77 8.22 13,537

6,146 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.68 7.78 13,598

6,840 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.71 7.81 13,566

6,465 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.65 7.85 13,597

6,840 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.74 7.8 13,608

6,529 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.7 7.9 13,566

6,844 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 7.8 13,589

6,518 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 7.92 13,585

6,726 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.74 8.01 13,596

6,513 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.64 8.09 13,513

6,929 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.66 8.19 13,459

6,446 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.36 13,474

6,773 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.72 8.32 13,468

6,257 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 7.96 13,613

6,792 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 7.86 13,637

6,974 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.11 13,585

6,989 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.07 13,565

6,966 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.68 8.44 13,447

6,710 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.67 8.22 13,498

6,489 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.7 8.6 13,481

6,466 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.71 8.9 13,391

6,585 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.93 8.55 13,458

6,552 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.72 8.58 13,454

6,596 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.62 8.63 13,456

6,414 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.45 13,448

6,383 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.84 13,402

6,551 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.66 8.87 13,413

6,450 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.65 8.67 13,468

6,416 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.63 9.28 13,304

6,307 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.65 9.09 13,404

6,404 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.65 8.87 13,428

6,406 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.67 9.22 13,382

6,443 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.63 9.24 13,357

6,214 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.65 8.69 13,443

6,593 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.65 9.22 13,352

6,525 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.62 8.91 13,434

6,446 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 9.02 13,371

6,556 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.68 8.85 13,469

6,746 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.72 9.17 13,428

7,179 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.68 9.23 13,405

7,040 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.64 8.46 13,487

6,866 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.7 8.69 13,505

6,889 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.71 8.59 13,511

7,179 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.69 8.42 13,459

7,032 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.72 8.32 13,530

6,667 4, 5, 6, 7 IL SALINE HARRISBURG #5 TRAIN 1.67 8.09 13,568

57,904 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.48 6.17 13,138

45,254 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.87 13,043

45,117 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.43 5.67 13,277

7,162 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 0.86 14.42 12,489

7,103 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.2 17.07 12,123

6,919 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.27 12.08 13,025

7,101 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.36 13.7 12,657

7,055 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.27 11.77 13,056

7,216 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.24 12.85 12,838

7,151 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.33 12.87 12,898

7,256 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.29 13.67 12,667

6,682 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.34 11.99 13,044

7,332 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.3 12.73 12,880
D.B. D.B. D.B.

State/Country County42 Coal seam43 % Sulf % Ash Btu/lb

Vendor Analyses

Amount received, dry Fuel source

basis, short tons40

ID # of boiler(s) firing 

fuel41

Fuel shipment 

method

7,282 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.26 12.35 12,920

7,414 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.29 11.06 13,212

7,421 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.24 10.99 13,161

7,509 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.34 11.6 13,149

7,409 4, 5, 6, 7 UT CARBON UPPER SUNNYSIDE TRAIN 1.28 11.73 13,063

7,190 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.51 11.14 12,733

7,177 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.5 9.13 13,029

7,259 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.5 10.05 12,981

7,265 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.53 10.14 13,019

6,661 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.45 7.76 13,570

6,441 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.45 9.41 13,222

6,509 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.45 8.17 13,424

6,509 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.45 8.17 13,424

6,539 4, 5, 6, 7 CO GUNNISON D SEAM TRAIN 0.45 11.61 12,866

6,689 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.08 10.51 12,902

7,314 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.12 9.96 13,043

4,884 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.36 10.35 12,940

7,352 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.33 10.23 13,010

7,300 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.26 10.13 13,073

7,156 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.26 11.68 12,755

7,270 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.24 10.37 13,021

7,305 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.29 9.87 12,940

7,194 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.25 10.07 13,086

7,275 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.22 10.37 13,002

7,291 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.21 9.8 13,032

7,307 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.23 9.89 13,041

7,227 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.18 9.71 13,127

7,230 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.23 9.72 13,132

7,256 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.2 9.05 13,202

7,127 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.22 9.95 13,062

7,263 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.29 9.78 13,096

7,209 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.3 9.61 13,051

7,278 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.18 9.15 13,105

7,144 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.19 9.51 13,114

7,218 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.16 9.91 13,108

7,084 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.27 10.1 13,100

7,363 4, 5, 6, 7 N/A EMERY N/A TRAIN 1.26 10.26 12,980

53,078 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.52 6.3 13,064

53,473 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.63 6.06 13,107

44,813 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.43 6 13,147

42,188 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.36 5.4 13,176

45,001 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.41 5.51 13,180

41,207 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.53 5.86 13,246

52,247 4, 5, 6, 7 COLOMBIA N/A GRAN MADRE SHIP 0.57 6.07 13,114

Note: "N/A" means not available.

Note: The information being provided is on a shipment by shipment basis. Gulf Power cannot guarantee that what was shipped in the preceding 12 calendar months is 

what was burned in the preceding 12 calendar months. 

40 EPA recognizes that facilities have (sometimes) several months inventory and that the amount received is not necessarily the same as the 

amount fired.

41 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

42 If known.

43 If known.
State/Country County42 Coal seam43

7,418 4, 5, 6, 7 Florida/USA N/A N/A Truck

7,434 4, 5, 6, 7 Florida/USA N/A N/A Truck

22,260 4, 5, 6, 7 Florida/USA N/A N/A Truck

14,856 4, 5, 6, 7 Florida/USA N/A N/A Truck

14,852 4, 5, 6, 7 Florida/USA N/A N/A Truck

14,816 4, 5, 6, 7 Florida/USA N/A N/A Truck

14,819 4, 5, 6, 7 Florida/USA N/A N/A Truck

7,410 4, 5, 6, 7 Florida/USA N/A N/A Truck

7,406 4, 5, 6, 7 Florida/USA N/A N/A Truck

14,841 4, 5, 6, 7 Florida/USA N/A N/A Truck

7,524 4, 5, 6, 7 Florida/USA N/A N/A Truck

15,025 4, 5, 6, 7 Florida/USA N/A N/A Truck

15,033 4, 5, 6, 7 Florida/USA N/A N/A Truck

22,503 4, 5, 6, 7 Florida/USA N/A N/A Truck

40 EPA recognizes that facilities have (sometimes) several months inventory and that the amount received is not necessarily the same as the 

amount fired.

41 Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, 

[for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW])

OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

42 If known.

43 If known.

FUEL OIL SHIPMENTS

Amount received, 

gallons40

ID # of boiler(s) firing 

fuel41

Fuel source Fuel shipment 

method
3 For each individual coal and oil shipment received during the preceding 12 calendar months, provide the following information44

, as

available (dry basis) (indicate N/A if not available):

Antimony Arsenic Beryllium Cadmium Chromium Cobalt Lead Manganese Selenium

09-303 11,951 1.3 13.76 12,684 0.053 378 76 4.8 <1 1.3 0.9 0.05 8.9 2.0 6.2 17.5 0.9 UT Carbon County Upper Sunnyside Train

09-707 79,833 0.57 6.76 13,037 0.118 37 85 5.2 1.2 6.1 0.5 0.17 6.2 2.2 2.9 15.3 5.3 COLOMBIA Cesar / La Loma Gran Madre Ship

09-306 11,746 0.55 10.55 12,773 0.028 76 59 4.0 <1 0.9 0.7 0.06 5.3 2.3 6.0 13.2 1.0 CO Gunnison D Train

09-801 11,240 1.84 8.42 13,467 0.173 4003 62 16.0 <1 24.6 1.2 0.10 10.3 5.6 42.5 16.0 1.0 IL Saline Herron # 5 Seam Train

09-802 10,928 1.75 8.2 13,570 0.027 4047 37 19.2 1.3 23.0 1.5 0.20 11.6 6.2 57.9 16.1 1.0 IL Saline Herron # 5 Seam Train

09-319 12,281 0.57 9.66 12,894 0.030 131 56 3.7 <1 1.0 0.6 0.03 5.0 2.1 5.4 21.7 0.9 CO Gunnison D Train

09-320 12,193 1.14 10.21 13,040 0.017 140 ND 3.7 <1 1.4 0.4 <0.02 5.3 2.2 4.4 19.0 0.8 UT Emery A,J, I Train

09-323 12,237 1.39 11.4 13,152 0.055 432 39 4.2 <1 0.8 0.6 0.09 8.5 1.8 5.2 11.9 1.2 UT Carbon County Upper Sunnyside Train

09-715 79,489 0.43 5.83 13,132 0.068 40 43 4.8 1.0 2.2 0.5 0.05 4.5 1.9 1.9 16.4 5.4 COLOMBIA Cesar / La Loma Gran Madre Ship

09-710 94,324 0.61 5.86 13,104 0.112 34 57 3.8 <1 4.4 0.4 0.15 5.0 1.6 2.3 14.3 5.8 COLOMBIA Cesar / La Loma Gran Madre Ship

09-333 12,286 0.53 10.91 13,086 0.033 231 57 4.0 <1 1.0 0.7 0.03 5.9 2.2 5.6 13.7 0.9 CO Gunnison D Train

09-803 11,375 1.7 8.26 13,516 0.153 3129 57 ND <1 ND <0.1 <0.02 <0.1 ND ND ND 1.0 IL Saline Herron # 5 seam Train

09-229 1,558 0.79 15.23 12,819 0.085 1845 84 17.0 1.3 5.8 3.1 <0.02 20.5 8.7 9.2 59.8 2.5 WV Kanawha Eagle, Stockton, Winifrede Barge

09-221 1,600 1.03 15.41 12,817 0.130 2147 64 16.3 1.0 10.0 2.7 <0.02 21.6 9.7 9.6 57.7 3.4 WV Kanawha Stockton, Eagle Barge

09-335 12,195 1.26 9.81 13,377 0.046 388 57 4.0 <1 0.9 0.8 0.05 7.8 1.8 4.8 12.5 1.1 UT Carbon County Upper Sunnyside Train

09-336 12,184 1.25 9.65 13,135 0.174 141 31 2.9 <1 1.5 0.3 <0.02 4.5 1.7 4.2 17.9 0.9 UT Emery "A","J", "I" Train

09-724 80,014 0.4 5.79 13,181 0.047 33 37 4.8 <1 2.1 0.4 0.11 5.4 2.2 2.6 18.5 5.2 COLOMBIA Cesar / La Loma Gran Madre Ship

09-338 12,197 0.46 9.97 13,087 0.032 266 56 4.1 <1 1.1 0.6 0.05 6.4 2.9 6.5 16.9 0.9 CO Gunnison "D" Train

09-339 12,192 1.18 10.07 13,013 0.174 161 26 3.3 <1 2.1 0.2 ND 5.7 2.2 4.6 19.3 0.9 UT Emery "A","J", "I" Train

09-804 12,321 1.71 8.72 13,475 0.142 3347 57 15.6 1.0 21.9 1.3 0.16 11.1 5.7 49.9 20.8 1.0 IL Saline Herron # 5 seam Train

09-350 12,181 1.36 11.53 13,153 0.051 472 33 3.9 <1 1.2 0.7 0.09 9.3 2.1 5.6 12.1 1.2 UT Carbon County Upper Sunnyside Train

09-528 1,549 0.84 13.88 13,072 0.057 1795 85 14.0 <1 8.8 3.4 ND 19.3 8.4 8.6 58.2 2.7 WV Kanawha Eagle, Stockton Barge

Note:

"ND" means non-detect.

Multiple seams may be listed to account for the flexibility written into the purchase orders. Actual shipments may not have originated from each seam listed.

Note: Gulf Power collects this information on select coal shipments, but does not have this information available on a shipment by shipment basis. The information Gulf Power provides in this response cannot be linked to the information in Part II, Question 2 because the information comes from two separate databases.

Thus, the information provided in this response represents only a very small portion of our actual shipments.

44 To the extent that a vendor provides these data or that a facility is required by State or local agency to analyze its fuel for HAP constituents (e.g., Cl, F), 

and any metallic HAP (e.g., Hg, Pb, As, Se, etc.), EPA wishes the responding facility to provide those fuel analyses results. Otherwise, this 12-month fuel

analysis requirement can be bypassed by the respondent.

45 Metal HAP includes compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium.

Fuel Shipment 

Method

Coal Seam Sample ID 

#

Total amount of 

fuel represented by 

sample, tons

Total 

Sulfur, %

Ash 

Content, % County Nickel, ppm

Other trace metal HAP, ppm45

State/Country Heating Value, 

Btu/lb

Mercury, 

ppm

Chlorine, 

ppm

Fluorine, 

ppm
4 Were the data provided in Part II, question 3 above, acquired pursuant to:

____ permit requirements

____ contractual obligations

____ standard operational procedures

_X__ other (please specify to support R&D projects, plant performance, and TRI reporting)

5 Analyses provided in Part II, question 3 above, supplied by

____ Fuel supplier (name and address)

_X__ Other (name and address)

Analytical services are conducted by Alabama Power Company's in-house laboratory.

Alabama Power Company, General Services Laboratory

744 Highway 87, GSC #8

Calera, AL 35040

6 Name and address of laboratory performing analyses:

Alabama Power Company, General Services Laboratory

744 Highway 87, GSC #8

Calera, AL 35040

7 In addition to the analyses required in Part II, question 3 above, for samples for which analyses of chlorine and/or any of the HAP metals were 

conducted, please provide copies of any analyses conducted over the preceding 12 calendar months for (a) complete proximate and ultimate 

analyses, (b) additional trace metals, and (c) the mineralogy of the ash that are readily available for the oil(s) or coal(s) listed in Part II, question

2 above. The Agency is requesting these data only as they may already be available; no additional sampling or analyses are required to provide

these data.

Total 

Moisture Volatiles Ash Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen Barium Copper Magnesium Sodium Vanadium Zinc Al2O3 Fe2O3 CaO MgO MnO2 P2O5 K2O SiO2 Na2O SO3 TiO2

09-303 6.64 35.56 13.76 50.68 73.51 4.72 1.5 1.3 5.21 100 5.0 0.161 0.033 10.3 10.4 13.34 4.28 5.76 1.94 0.02018 0.5 0.82 65.01 0.33 7.56 0.62

09-707 12.18 38.71 6.76 54.53 76.46 4.64 1.46 0.57 10.11 250 6.3 0.060 0.122 18.9 9.9 20.53 6.94 3.21 1.47 0.03578 0.28 1.51 56.92 2.42 5.39 0.8

09-306 8.8 38.09 10.55 51.36 74.14 4.84 1.54 0.55 8.38 240 8.5 0.081 0.050 15.5 11.0 27.37 5.02 3.32 1.27 0.01981 0.62 1.35 55.88 0.63 3.3 0.86

09-801 11.23 34.57 8.42 57.01 76.35 4.98 1.78 1.84 6.63 30 7.2 0.046 0.066 18.2 17.8 19.58 19.25 1.9 0.91 0.0301 0.48 2.38 51.3 1.05 1.81 1.22

09-802 11.89 34.32 8.2 57.48 76.87 4.98 1.75 1.75 6.45 40 8.6 0.046 0.065 20.8 33.2 19.88 17.13 2.07 0.93 0.03108 0.55 2.48 52.67 1.06 1.81 1.25

09-319 8.81 37.86 9.66 52.48 72.92 5.03 1.64 0.57 10.18 250 8.2 0.075 0.051 14.2 14.4 25.88 6.26 4.06 1.3 0.0355 0.68 1.37 54.6 0.72 3.76 0.9

09-320 6.97 38.51 10.21 51.28 74.04 5.02 1.26 1.14 8.33 120 7.0 0.151 0.121 9.5 3.7 16.51 6.43 10.19 2.46 0.02948 0.17 0.36 47.95 1.6 13.04 0.95

09-323 5.84 36.06 11.4 52.54 73.68 4.99 1.56 1.39 6.98 170 4.7 0.078 0.035 10.2 9.7 16.05 4.29 4.73 1.13 0.01657 0.43 0.94 66.25 0.42 4.73 0.83

09-715 11.77 39.36 5.83 54.81 75.74 5.05 1.51 0.43 11.44 230 4.9 0.055 0.117 13.1 6.8 18.89 7.21 3.29 1.58 0.04447 0.17 1.29 57.59 2.7 5.77 0.92

09-710 12.44 39.1 5.86 55.04 76.29 4.93 1.51 0.61 10.8 230 5.6 0.054 0.107 16.2 6.6 20.85 8.66 3.72 1.54 0.03871 0.38 1.38 54.11 2.47 5.31 0.99

09-333 7.58 36.91 10.91 52.18 73.35 5.03 1.34 0.53 8.84 240 9.0 0.079 0.074 15.5 10.6 23.62 5.05 3.01 1.2 0.01991 0.52 1.83 59.66 0.92 2.96 0.89

09-803 10.29 34.27 8.26 57.47 76.93 4.94 1.68 1.7 6.49 30 ND 0.049 0.060 ND ND 20.47 15.45 1.9 0.98 0.0311 0.57 2.55 53.58 0.98 2.13 1.25

09-320 6.97 38.51 10.21 51.28 74.04 5.02 1.26 1.14 8.33 120 7.0 0.151 0.121 9.5 3.7 16.51 6.43 10.19 2.46 0.02948 0.17 0.36 47.95 1.6 13.04 0.95

09-229 8.43 30.75 15.23 54.02 72.98 4.66 1.26 0.79 5.08 110 17.7 0.101 0.050 34.6 21.5 26.09 6.18 1.06 1.1 0.06211 0.14 3.67 58.63 0.45 1.05 1.47

09-221 6.75 30.44 15.41 54.15 72.9 4.66 1.37 1.03 4.63 80 20.4 0.088 0.045 33.9 20.7 25.01 7.14 1.21 0.95 0.05926 0.09 2.8 59.26 0.39 1.54 1.47

09-335 5.25 36.46 9.81 53.73 75.43 5.05 1.49 1.26 6.96 140 4.6 0.064 0.032 9.0 8.7 15.19 4.69 5.03 1.07 0.02019 0.75 0.79 65.79 0.45 5.19 0.81

09-336 6.97 38.51 9.65 51.84 74.2 5.04 1.12 1.25 8.74 130 6.5 0.129 0.101 8.2 3.5 14.59 7 10.56 2.23 0.02931 0.14 0.38 49.99 1.42 12.94 0.9

09-724 12.5 39.34 5.79 54.87 75.63 5.22 1.48 0.4 11.48 240 6.2 0.060 0.107 16.1 8.5 20.16 7.34 3.96 1.71 0.05069 0.19 1.49 55.4 2.5 5.7 0.97

09-338 7.8 37.33 9.97 52.7 73.85 5.15 1.71 0.46 8.86 220 9.9 0.078 0.071 17.6 13.6 24.33 5.36 4.07 1.3 0.0269 0.54 1.55 56.81 0.96 3.78 0.93

09-339 6.94 38.03 10.07 51.9 73.71 5.04 1.36 1.18 8.64 130 6.7 0.125 0.111 9.6 5.5 14.64 7.67 9.81 2.06 0.03026 0.12 0.43 50.38 1.48 12.16 0.94

09-804 10.35 34.75 8.72 56.53 75.97 4.97 1.85 1.71 6.78 20 8.0 0.052 0.065 18.3 29.4 19.18 14.88 2.33 0.99 0.03776 0.56 2.39 54.67 1.01 2.64 1.21

09-350 5.18 35.68 11.53 52.79 73.64 5.11 1.65 1.36 6.71 140 4.4 0.082 0.033 10.3 11.0 15.33 4.58 4.77 1.17 0.01657 0.54 1.08 66.26 0.39 4.85 0.81

09-528 8.19 31.76 13.88 54.35 73.22 4.55 1.31 0.84 6.2 91 16.8 0.084 0.045 30.5 18.1 22.6 6.04 1.77 0.992 ND ND 2.65 56.4 0.498 1.15 1.53

Note: "ND" means non-detect.

Sample ID 

#

Proximate Analyses, % by wt Ultimate Analyses, % by wt Other Trace Metals, ppm Ash Mineralogy, % by wt
8a What emission test report(s), parametric monitoring data, and other data or monitoring are available for the boilers noted in Part I,

question 15, for tests conducted since January 1, 2005. Please consider reports prepared for all testing and monitoring programs, for

all pollutants, including (but not limited to) those required under Title V, compliance with State or local requirements, fulfillment of

contractual obligations, U.S. Department of Energy (DOE) programs, etc. (NOTE: EPA is not requesting copies of the test reports or data

at this time; however we may request actual copies in the future.) Use additional pages as necessary.

Report 1 Crist 4 1/27/2005 Particulate Soot Blow Test 

Report 2 1/28/2005 Particulate Steady State Test 

Report 3 4/18/2005 Unit 4 SO2 Test

Report 4 Crist 5 1/25/2005 Unit 5 SO2 Test

Report 5 1/25/2005 Particulate Soot Blow Test 

Report 6 1/26/2005 Particulate Steady State Test 

Report 7 Crist 6 3/8/2005 Particulate Soot Blow Test 

Report 8 3/9/2005 Particulate Steady State Test 

Report 9 3/17/2005 Unit 6 SO2 Test

Report 10 Crist 7 6/28/2005 Particulate Steady State Test 

Report 11 6/29/2005 Particulate Soot Blow Test 

Report 12 9/22/2005 Particulate Soot Blow Test 

Report 13 9/23/2005 Particulate Steady State Test 

Report 14 9/27/2005 Unit 7 SO2 Test

Report 15 12/6/2005 Particulate Steady State Test 

Report 16 Crist 4 5/31/2006 Particulate Soot Blow Test 

Report 17 5/31/2006 Particulate Steady State Test 

Report 18 6/1/2006 SO2, NOX Test

Report 19 6/1/2006 Unit 4 SO2 Test

Report 20 9/21/2006 SAM Test

Report 21 Crist 5 1/24/2006 Unit 5 SO2 Test

Report 22 1/24/2006 Particulate Soot Blow Test 

Report 23 1/25/2006 Particulate Steady State Test 

Report 24 9/20/2006 SAM Test

Report 25 Crist 6 2/24/2006 Unit 6 SO2 Test

Report 26 3/6/2006 Particulate Soot Blow Test 

Report 27 3/6/2006 Particulate Steady State Test 

Report 28 9/19/2006 SAM Test

Report 29 Crist 7 6/13/2006 Particulate Soot Blow Test 

Report 30 6/13/2006 Particulate Steady State Test 

Report 31 9/12/2006 Unit 7 SO2 Test

Report 32 9/18/2006 SAM Test

Report 33 Crist 4 5/1/2007 Unit 4 SO2 Test

Report 34 5/1/2007 Particulate Soot Blow Test 

Report 35 5/1/2007 Particulate Steady State Test 

Report 36 Crist 5 1/23/2007 Unit 5 SO2 Test

Report 37 1/23/2007 Particulate Soot Blow Test 

Report 38 1/23/2007 Particulate Steady State Test 

Report 39 11/12/2007 Particulate Steady State Test 

Report 40 11/13/2007 Particulate Steady State Test 

Report 41 Crist 6 2/16/2007 Unit 6 SO2 Test

Report 42 2/20/2007 Particulate Soot Blow Test 

Report 43 2/20/2007 Particulate Steady State Test 

Report 44 Crist 7 1/12/2007 Boiler Test - APH Performance

Report 45 3/9/2007 Particulate Steady State Test 

Report 46 9/25/2007 Unit 7 SO2 Test

Report 47 9/25/2007 Particulate Soot Blow Test 

Report 48 9/26/2007 Particulate Steady State Test 

Report 49 Crist 4 4/29/2008 Unit 4 SO2 Test

Report 50 4/29/2008 Particulate Soot Blow Test 

Report 51 4/29/2008 Particulate Steady State Test 

Report 52 6/5/2008 Particulate Inlet/Outlet Side A

Report 53 6/5/2008 Particulate Inlet/Outlet Side B

Report 54 Crist 5 4/9/2008 Unit 5 SO2 Test

Report 55 4/9/2008 Particulate Soot Blow Test 

Report 56 4/9/2008 Particulate Steady State Test 

Report 57 5/15/2008 Particulate Inlet/Outlet Side A

Report 58 5/15/2008 Particulate Inlet/Outlet Side B
Report 59 Crist 6 5/20/2008 Unit 6 SO2 Test

Report 60 5/20/2008 Particulate Soot Blow Test 

Report 61 5/20/2008 Particulate Steady State Test 

Report 62 Crist 7 5/13/2008 Unit 7 SO2 Test

Report 63 5/13/2008 Particulate Soot Blow Test 

Report 64 5/14/2008 Particulate Steady State Test 

Report 65 Crist 4 2/3/2009 Unit 4 SO2 Test

Report 66 2/3/2009 Particulate Soot Blow Test 

Report 67 2/3/2009 Particulate Steady State Test 

Report 68 Crist 5 2/17/2009 Unit 5 SO2 Test

Report 69 2/17/2009 Particulate Soot Blow Test 

Report 70 2/17/2009 Particulate Steady State Test 

Report 71 Crist 6 5/11/2009 Unit 6 SO2 Test

Report 72 5/11/2009 Particulate Soot Blow Test 

Report 73 5/12/2009 Particulate Steady State Test 

Report 74 7/23/2009 Boiler Test - Coal Conveyence

Report 75 Crist 7 4/20/2009 Particulate Steady State Test 

Report 76 4/22/2009 Particulate Soot Blow Test 

Report 77 4/22/2009 Unit 7 SO2 Test

8b Please indicate the date(s) and types (e.g., stack, fuel, parametric, etc.) of the test(s) and the constituents (including criteria and hazardous

air pollutants) sampled for:

Report 1 Date: 1/27/2005 Type: Duct Constituents: PM

Report 2 Date: 1/28/2005 Type: Duct Constituents: PM

Report 3 Date: 4/18/2005 Type: Duct Constituents: SO2

Report 4 Date: 1/25/2005 Type: Duct Constituents: SO2

Report 5 Date: 1/25/2005 Type: Duct Constituents: PM

Report 6 Date: 1/26/2005 Type: Duct Constituents: PM

Report 7 Date: 3/8/2005 Type: Duct Constituents: PM

Report 8 Date: 3/9/2005 Type: Duct Constituents: PM

Report 9 Date: 3/17/2005 Type: Duct Constituents: SO2

Report 10 Date: 6/28/2005 Type: Duct Constituents: PM

Report 11 Date: 6/29/2005 Type: Duct Constituents: PM

Report 12 Date: 9/22/2005 Type: Duct Constituents: PM

Report 13 Date: 9/23/2005 Type: Duct Constituents: PM

Report 14 Date: 9/27/2005 Type: Duct Constituents: SO2

Report 15 Date: 12/6/2005 Type: Duct Constituents: PM

Report 16 Date: 5/31/2006 Type: Duct Constituents: PM

Report 17 Date: 5/31/2006 Type: Duct Constituents: PM

Report 18 Date: 6/1/2006 Type: Duct Constituents: SO2,NOx,O2.CO2

Report 19 Date: 6/1/2006 Type: Duct Constituents: SO2

Report 20 Date: 9/21/2006 Type: Duct Constituents: H2SO4

Report 21 Date: 1/24/2006 Type: Duct Constituents: SO2

Report 22 Date: 1/24/2006 Type: Duct Constituents: PM

Report 23 Date: 1/25/2006 Type: Duct Constituents: PM

Report 24 Date: 9/20/2006 Type: Duct Constituents: H2SO4

Report 25 Date: 2/24/2006 Type: Duct Constituents: SO2

Report 26 Date: 3/6/2006 Type: Duct Constituents: PM

Report 27 Date: 3/6/2006 Type: Duct Constituents: PM

Report 28 Date: 9/19/2006 Type: Duct Constituents: H2SO4

Report 29 Date: 6/13/2006 Type: Duct Constituents: PM

Report 30 Date: 6/13/2006 Type: Duct Constituents: PM

Report 31 Date: 9/12/2006 Type: Duct Constituents: SO2

Report 32 Date: 9/18/2006 Type: Duct Constituents: H2SO4

Report 33 Date: 5/1/2007 Type: Duct Constituents: SO2

Report 34 Date: 5/1/2007 Type: Duct Constituents: PM

Report 35 Date: 5/1/2007 Type: Duct Constituents: PM

Report 36 Date: 1/23/2007 Type: Duct Constituents: SO2
Report 37 Date: 1/23/2007 Type: Duct Constituents: PM

Report 38 Date: 1/23/2007 Type: Duct Constituents: PM

Report 39 Date: 11/12/2007 Type: Duct Constituents: PM

Report 40 Date: 11/13/2007 Type: Duct Constituents: PM

Report 41 Date: 2/16/2007 Type: Duct Constituents: SO2

Report 42 Date: 2/20/2007 Type: Duct Constituents: PM

Report 43 Date: 2/20/2007 Type: Duct Constituents: PM

Report 44 Date: 1/12/2007 Type: Duct Constituents: O2,CO,CO2

Report 45 Date: 3/9/2007 Type: Duct Constituents: PM

Report 46 Date: 9/25/2007 Type: Duct Constituents: SO2

Report 47 Date: 9/25/2007 Type: Duct Constituents: PM

Report 48 Date: 9/26/2007 Type: Duct Constituents: PM

Report 49 Date: 4/29/2008 Type: Duct Constituents: SO2

Report 50 Date: 4/29/2008 Type: Duct Constituents: PM

Report 51 Date: 4/29/2008 Type: Duct Constituents: PM

Report 52 Date: 6/5/2008 Type: Duct Constituents: PM

Report 53 Date: 6/5/2008 Type: Duct Constituents: PM

Report 54 Date: 4/9/2008 Type: Duct Constituents: SO2

Report 55 Date: 4/9/2008 Type: Duct Constituents: PM

Report 56 Date: 4/9/2008 Type: Duct Constituents: PM

Report 57 Date: 5/15/2008 Type: Duct Constituents: PM

Report 58 Date: 5/15/2008 Type: Duct Constituents: PM

Report 59 Date: 5/20/2008 Type: Duct Constituents: SO2

Report 60 Date: 5/20/2008 Type: Duct Constituents: PM

Report 61 Date: 5/20/2008 Type: Duct Constituents: PM

Report 62 Date: 5/13/2008 Type: Duct Constituents: SO2

Report 63 Date: 5/13/2008 Type: Duct Constituents: PM

Report 64 Date: 5/14/2008 Type: Duct Constituents: PM

Report 65 Date: 2/3/2009 Type: Duct Constituents: SO2

Report 66 Date: 2/3/2009 Type: Duct Constituents: PM

Report 67 Date: 2/3/2009 Type: Duct Constituents: PM

Report 68 Date: 2/17/2009 Type: Duct Constituents: SO2

Report 69 Date: 2/17/2009 Type: Duct Constituents: PM

Report 70 Date: 2/17/2009 Type: Duct Constituents: PM

Report 71 Date: 5/11/2009 Type: Duct Constituents: SO2

Report 72 Date: 5/11/2009 Type: Duct Constituents: PM

Report 73 Date: 5/12/2009 Type: Duct Constituents: PM

Report 74 Date: 7/23/2009 Type: Duct Constituents: O2,CO,CO2

Report 75 Date: 4/20/2009 Type: Duct Constituents: PM

Report 76 Date: 4/22/2009 Type: Duct Constituents: PM

Report 77 Date: 4/22/2009 Type: Duct Constituents: SO2

8c Do any of these test reports reflect testing at a location upstream of any emission control devices?

Yes __X__ No ____ If yes, please note which reports and provide a detailed description of the location of the emissions sampling point(s).

Report 44 Crist 7 1/12/2007 Boiler APH Performance Test

Report 52 Crist 4 6/5/2008 Inlet/Outlet Side A ESP

Report 53 Crist 4 6/5/2008 Inlet/Outlet Side A ESP

Report 57 Crist 5 5/15/2008 Inlet/Outlet Side A ESP

Report 58 Crist 5 5/15/2008 Inlet/Outlet Side A ESP

Report 74 Crist 6 7/23/2009 Boiler Test - Coal Conveyence

8d Were any of these test reports conducted when use of other material(s) or non-fossil fuels were fired in the boiler?

Yes ____ No _X__ If yes, please not which reports and identify the other material(s) or non-fossil fuels used.

8e Do any of these test reports reflect testing during periods of startup, shutdown, and malfunction?

Yes ____ No _X __ If yes, please note which reports.
8f Did the unit's control configuration differ from that shown in Part I, question 16, at the time of these test results?

Yes _X__ No ____ If yes, please list the unit's complete control configuration at time of testing in a similar format to Part I, question 16.

8f.1 All tests presented in Test Reports 1-9 were conducted with the same control configuration as outlined in the Table 8f-1 below: 

Table 8f-1 (Plant Configuration between 01/2005 - 04/2005)

Boiler ID14 Type15 NOx control16 SO2 control17 PM control18 Other control19

4 tangential - 

fired

1)low NOx burner tips (1998) N/A 2) Cold side ESP (01/1976) N/A

5 tangential - 

fired

1) low NOx burner tips (1998) N/A 2) Cold side ESP (01/1976) N/A

6 wall-fired 1) low NOx burner (1994) N/A 2) Cold side ESP (01/1994) N/A

7 wall-fired 1) low NOx burner (5/2004) N/A 2) Cold side ESP (04/2004) N/A

x) order of control Note: "N/A" means not applicable.

8f.2 All tests presented in Test Reports 10-14 were conducted with the same control configuration as outlined in the Table 8f-2 below: 

Table 8f-2 (Plant Configuration between 4/2005 - 11/2005)

Boiler ID14 Type15 NOx control16 SO2 control17 PM control18 Other control19

4 tangential - 

fired

1)low NOx burner tips (1998) N/A 2) Cold side ESP (01/1976) N/A

5 tangential - 

fired

1) low NOx burner tips (1998) N/A 2) Cold side ESP (01/1976) N/A

6 wall-fired 1) low NOx burner (1994) N/A 2) Cold side ESP (01/1994) N/A

7 wall-fired 1) low NOx burner (5/2004) 

2)SCR (04/2005)

N/A 3) Cold side ESP (04/2004) N/A

x) order of control Note: "N/A" means not applicable.

8f.3 All tests presented in Test Reports 15- 27 were conducted with the same control configuration as outlined in the Table 8f-3 below: 

Table 8f-3 (Plant Configuration between 11/2005-4/2006)

Boiler ID14 Type15 NOx control16 SO2 control17 PM control18 Other control19

4 tangential - 

fired

1) low NOx burner tips (1998) N/A 3) Cold side ESP (01/1976) N/A

5 tangential - 

fired

1) low NOx burner tips (1998) N/A 3) Cold side ESP (01/1976) N/A

6 wall-fired 1) low NOx burner (11/2005) 

2) SNCR (11/2005) 

N/A 3) Cold side ESP (01/1994) N/A

7 wall-fired 1) low NOx burner (5/2004) 

2) SCR (04/2005)

N/A 3) Cold side ESP (04/2004) N/A

x) order of control Note: "N/A" means not applicable.

8f.4 All tests presented in Test Reports 28-77 were conducted with the same control configuration as outlined in the Table 8f-4 below: 

Table 8f-4 (Plant Configuration between 04/2006-12/2009)

Boiler ID14 Type15 NOx control16 SO2 control17 PM control18 Other control19

4 tangential - 

fired

1) low NOx burner tips (1998) 

2) SNCR (4/2006)

N/A 3) hot side ESP (rebuilt in 

3/2008) 

4) Cold side ESP (01/1976)

N/A

5 tangential - 

fired

1) low NOx burner tips (1998) 

2) SNCR (4/2006)

N/A 3) hot side ESP (rebuilt in 

3/2008) 

4) Cold side ESP (01/1976)

N/A

6 wall-fired 1) low NOx burner (11/2005) 

2) SNCR (11/2005) 

N/A 3) Cold side ESP (01/1994) N/A

7 wall-fired 1) low NOx burner (5/2004) 

2) SCR (04/2005)

N/A 3) Cold side ESP (04/2004) N/A

Note: "N/A" means not applicable.

8g Do any of these test reports reflect testing at a location upstream of a post combustion SO2 emission control device (e.g., FGD, SDA, Dry Scrubber)?

Yes ____ No _X__ If yes, please note which reports and, in addition to the detailed description of the location of the sampling point(s)

(question 8c above), include detail about how much, if any, bypass of unscrubbed flue gas was utilized at at the time of testing (including
percentage of total scrubber flue gas flow). Note by diagram where sampling ports were located in relation to the bypass ductwork.
9 What type of deviation reporting is required for violations of permit requirements?

Deviations which constitute a violation from permit conditions shall be reported immediately to FDEP. Immediately 

shall mean the same workday (i.e. 8:00 am to 5:00 pm), or first business day after the incident,excluding weekends and holidays.

This report shall contain a description of and cause of noncompliance; and the period of noncompliance, including dates and times; 

weekends and holidays. This report shall contain a description of and cause of noncompliance; and the period of noncompliance,

including dates and times; or if not corrected, the anticipated time the noncompliance is expected to continue, and steps being 

taken to reduce, eliminate, and prevent the recurrence of the noncompliance. The permittee shall be responsible for any and 

all damages which may result and may be subjext to enforcement action by the Department for penalties or revocation of the permit. 

Deviations which do not constitute a violation as allowable excess emissions are reported quarterly or semi-annual under 

the Excess Emissions, Semi-annual Monitoring and Annual Title V Certification Reports. 

10 Are deviation reports available for malfunctions or other periods of noncompliance with permit terms and conditions?

Yes _X__ No ____ If yes, please note which reports.

Deviations from any permit condition is reported in the Semi-annual monitoring reports submitted to FDEP. 

11 Are continuous emissions monitoring system (CEMS) data available (e.g., mercury, continuous opacity monitoring systems) that are not

already being provided to the U.S. EPA, even if from short-term testing?

Yes _X__ No ____ If yes46, please note for which pollutants CEMS data are available and the period of time (both total period and calendar

period) for which the data are available. If CEM data are being provided to EPA, please note to which Office the data are being provided.

Report 78 08/24/05 - 08/28/05 Unit 6: Multi-Method Mercury Speciation Testing Under Various Operations1 

Report 79 02/18/08 - 02/29/08 Unit 6 & 7: EPA/EPRI/DOE Crist Blimp Study1

01/01/05 - 12/31/09 Unit 4: Continuous Opacity Monitoring Information is available upon request

01/01/05 - 12/31/09 Unit 5: Continuous Opacity Monitoring Information is available upon request

01/01/05 - 12/31/09 Unit 6: Continuous Opacity Monitoring Information is available upon request

01/01/05 - 12/31/09 Unit 7: Continuous Opacity Monitoring Information is available upon request

1

 Gulf Power considers CEMS data "available" only if it is maintained and subject to quality assurance/quality control

46 Where units are monitored by CEMs (either following CAMR, State, or NIST QA/QC procedures), and where data are available, EPA requests

that this CEM data by submitted by the respondent. The respondent should also mark the periods of start up, shut down and malfunction events (SSM) in the data sets.
12 For each boiler noted in Part I, question 15, provide the following information:

Test Report Date of test PM49 SO2 HCl/HF/HCN Metal HAP50 Hg51 CO Other organics 

(specify)

Crist 4 Report 1 1/27/2005 See Attachment 1 N/A N/A N/A N/A N/A N/A

Report 2 1/28/2005 See Attachment 2 N/A N/A N/A N/A N/A N/A

Report 3 4/18/2005 N/A See Attachment 3 N/A N/A N/A N/A N/A

Crist 5 Report 4 1/25/2005 N/A See Attachment 4 N/A N/A N/A N/A N/A

Report 5 1/25/2005 See Attachment 5 N/A N/A N/A N/A N/A N/A

Report 6 1/26/2005 See Attachment 6 N/A N/A N/A N/A N/A N/A

Crist 6 Report 7 3/8/2005 See Attachment 7 N/A N/A N/A N/A N/A N/A

Report 8 3/9/2005 See Attachment 8 N/A N/A N/A N/A N/A N/A

Report 9 3/17/2005 N/A See Attachment 9 N/A N/A N/A N/A N/A

Crist 7 Report 10 6/28/2005 See Attachment 10 N/A N/A N/A N/A N/A N/A

Report 11 6/29/2005 See Attachment 11 N/A N/A N/A N/A N/A N/A

Report 12 9/22/2005 See Attachment 12 N/A N/A N/A N/A N/A N/A

Report 13 9/23/2005 See Attachment 13 N/A N/A N/A N/A N/A N/A

Report 14 9/27/2005 N/A See Attachment 14 N/A N/A N/A N/A N/A

Report 15 12/6/2005 See Attachment 15 N/A N/A N/A N/A N/A N/A

Crist 4 Report 16 5/31/2006 See Attachment 16 N/A N/A N/A N/A N/A N/A

Report 17 5/31/2006 See Attachment 17 N/A N/A N/A N/A N/A N/A

Report 18 6/1/2006 N/A See Attachment 18 N/A N/A N/A N/A N/A

Report 19 6/1/2006 N/A See Attachment 19 N/A N/A N/A N/A N/A

Report 20 9/21/2006 N/A N/A N/A N/A N/A N/A N/A

Crist 5 Report 21 1/24/2006 N/A See Attachment 21 N/A N/A N/A N/A N/A

Report 22 1/24/2006 See Attachment 22 N/A N/A N/A N/A N/A N/A

Report 23 1/25/2006 See Attachment 23 N/A N/A N/A N/A N/A N/A

Report 24 9/20/2006 N/A N/A N/A N/A N/A N/A N/A

Crist 6 Report 25 2/24/2006 N/A See Attachment 25 N/A N/A N/A N/A N/A

Report 26 3/6/2006 See Attachment 26 N/A N/A N/A N/A N/A N/A

Report 27 3/6/2006 See Attachment 27 N/A N/A N/A N/A N/A N/A

Report 28 9/19/2006 N/A N/A N/A N/A N/A N/A N/A

Crist 7 Report 29 6/13/2006 See Attachment 29 N/A N/A N/A N/A N/A N/A

Report 30 6/13/2006 See Attachment 30 N/A N/A N/A N/A N/A N/A

Report 31 9/12/2006 N/A See Attachment 31 N/A N/A N/A N/A N/A

Report 32 9/18/2006 N/A N/A N/A N/A N/A N/A N/A

Crist 4 Report 33 5/1/2007 N/A See Attachment 33 N/A N/A N/A N/A N/A

Report 34 5/1/2007 See Attachment 34 N/A N/A N/A N/A N/A N/A

Report 35 5/1/2007 See Attachment 35 N/A N/A N/A N/A N/A N/A

Crist 5 Report 36 1/23/2007 N/A See Attachment 36 N/A N/A N/A N/A N/A

Report 37 1/23/2007 See Attachment 37 N/A N/A N/A N/A N/A N/A

Report 38 1/23/2007 See Attachment 38 N/A N/A N/A N/A N/A N/A

Report 39 11/12/2007 See Attachment 39 N/A N/A N/A N/A N/A N/A

Report 40 11/13/2007 See Attachment 40 N/A N/A N/A N/A N/A N/A

Crist 6 Report 41 2/16/2007 N/A See Attachment 41 N/A N/A N/A N/A N/A

Report 42 2/20/2007 See Attachment 42 N/A N/A N/A N/A N/A N/A

Report 43 2/20/2007 See Attachment 43 N/A N/A N/A N/A N/A N/A

Crist 7 Report 44 1/12/2007 N/A N/A N/A N/A N/A See Attachment 44 N/A

Report 45 3/9/2007 See Attachment 45 N/A N/A N/A N/A N/A N/A

Report 46 9/25/2007 N/A See Attachment 46 N/A N/A N/A N/A N/A

Report 47 9/25/2007 See Attachment 47 N/A N/A N/A N/A N/A N/A

Boiler ID

Emissions test results (indicate format of emission data)47,48
Test Report Date of test PM49 SO2 HCl/HF/HCN Metal HAP50 Hg51 CO Other organics 

(specify)

Boiler ID

Emissions test results (indicate format of emission data)47,48

Report 48 9/26/2007 See Attachment 48 N/A N/A N/A N/A N/A N/A

Crist 4 Report 49 4/29/2008 N/A See Attachment 49 N/A N/A N/A N/A N/A

Report 50 4/29/2008 See Attachment 50 N/A N/A N/A N/A N/A N/A

Report 51 4/29/2008 See Attachment 51 N/A N/A N/A N/A N/A N/A

Report 52 6/5/2008 See Attachment 52 N/A N/A N/A N/A N/A N/A

Report 53 6/5/2008 See Attachment 53 N/A N/A N/A N/A N/A N/A

Crist 5 Report 54 4/9/2008 N/A See Attachment 54 N/A N/A N/A N/A N/A

Report 55 4/9/2008 See Attachment 55 N/A N/A N/A N/A N/A N/A

Report 56 4/9/2008 See Attachment 56 N/A N/A N/A N/A N/A N/A

Report 57 5/15/2008 See Attachment 57 N/A N/A N/A N/A N/A N/A

Report 58 5/15/2008 See Attachment 58 N/A N/A N/A N/A N/A N/A

Crist 6 Report 59 5/20/2008 N/A See Attachment 59 N/A N/A N/A N/A N/A

Report 60 5/20/2008 See Attachment 60 N/A N/A N/A N/A N/A N/A

Report 61 5/20/2008 See Attachment 61 N/A N/A N/A N/A N/A N/A

Crist 7 Report 62 5/13/2008 N/A See Attachment 62 N/A N/A N/A N/A N/A

Report 63 5/13/2008 See Attachment 63 N/A N/A N/A N/A N/A N/A

Report 64 5/14/2008 See Attachment 64 N/A N/A N/A N/A N/A N/A

Crist 4 Report 65 2/3/2009 N/A See Attachment 65 N/A N/A N/A N/A N/A

Report 66 2/3/2009 See Attachment 66 N/A N/A N/A N/A N/A N/A

Report 67 2/3/2009 See Attachment 67 N/A N/A N/A N/A N/A N/A

Crist 5 Report 68 2/17/2009 N/A See Attachment 68 N/A N/A N/A N/A N/A

Report 69 2/17/2009 See Attachment 69 N/A N/A N/A N/A N/A N/A

Report 70 2/17/2009 See Attachment 70 N/A N/A N/A N/A N/A N/A

Crist 6 Report 71 5/11/2009 N/A See Attachment 71 N/A N/A N/A N/A N/A

Report 72 5/11/2009 See Attachment 72 N/A N/A N/A N/A N/A N/A

Report 73 5/12/2009 See Attachment 73 N/A N/A N/A N/A N/A N/A

Report 74 7/23/2009 N/A N/A N/A N/A N/A See Attachment 74 N/A

Crist 7 Report 75 4/20/2009 See Attachment 75 N/A N/A N/A N/A N/A N/A

Report 76 4/22/2009 See Attachment 76 N/A N/A N/A N/A N/A N/A

Report 77 4/22/2009 N/A See Attachment 77 N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

47 Provide emission test data for all tests conducted since January 1, 2005. Please indicate test data acquired both before and after

any control device. Use additional pages as necessary. EPA may, at some future date, request a copy of one or more emission test reports.

Data generated to fulfill both Federal and State requirements must be provided. Note that data generated pursuant to CAA Title V

must be maintained and available for 5 years. Also include averaging times and measurement units for all pollutants.

48 For each emissions test run the respondent should provide the following process information: Unit Load (MW), Net generation during run (MWh net),

Flue gas moisture content (%), Flue gas flow rate (dscfm or Nm3/hr), Flue gas oxygen content (%, dry), Flue gas carbon dioxide content (%, dry), Flue gas

temperature at sampling point (oF), Flue gas pressure at sampling point (atm), Standard temperature (oF), Standard pressure (atm).

49 If emission testing recorded the emissions of filterable and condensable PM, separately, please include those separate emission results. 

Also, please include separate emission results for total PM, PM10, and PM2.5.

50 Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium;

indicate emission level for all metal HAP for which an emission test has been conducted.

51 Please provide separate results for total Hg, elemental Hg, oxidized Hg, and particulate Hg, as available. If the emissions testing recorded

the amount of unburned carbon in fly ash (as reflected by the "Loss of Ignition" [L.O.I]) at the time of any Hg testing, please include these data.
ATTACHMENT 1 - Crist Report 1 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/27/2005 1/27/2005 1/27/2005

Sampling Time -Start Military 0705 0835 1002

Sampling Time -Stop Military 0815 0945 1112

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.90 -0.90 -0.90

Barometric Pressure Inches Mercury 30.30 30.30 30.30

Meter Correction Factor dimensionless 1.011 1.011 1.011

Oxygen Concentration Mole Percent O2 6.0 6.5 6.0

Carbon Dioxide Concentration Mole Percent CO2 12.0 12.0 12.5

Volume of Gas Metered Actual Cubic Feet 33.570 34.662 35.568

Volume of Water Collected Milliliters 68 72 75

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.215 0.220 0.220

Weight of Solids Collected Milligrams 7.0 5.4 6.8

Area of Stack Square Feet 89.168 89.168 89.168

Avg. Sqr. Root Velocity Pressure Inches Water 0.8262 0.8245 0.8469

Average Orifice Pressure (H) Inches Water 1.0 1.1 1.2

Average Stack Temperature Degrees F 282 283 285

Average Meter Temperature Degrees F 58 60 63

3 Runs

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 35.142 36.164 36.905 36.070

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.14 29.14 29.17 29.15

Water vapor in Stack Gas Percent 8.3 8.6 8.7 8.5

Average Stack Gas Velocity Feet per second 54.4 54.4 55.9 54.9

Stack Gas Flow Rate Actual Cubic 291,293 290,860 299,042 293,732

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 209,295 208,842 214,032 210,723

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,823 190,948 195,346 192,706

 Feet Per Minute

Particulate Concentration Grains per Standard 0.0031 0.0023 0.0028 0.0027

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0020 0.0015 0.0019 0.0018

 Cubic Foot

Particulate Emission Rate Pounds per Hour 5.0 3.8 4.8 4.5

Particulate Emission Rate Pounds per Million 0.006 0.005 0.006 0.005

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 839 807 854 834

Isokinetic Rate Percent 101.2 99.9 99.7 100.3

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 4

SOOT BLOWING OPERATIONS
ATTACHMENT 2 - Crist Report 2 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/28/2005 1/28/2005 1/28/2005

Sampling Time -Start Military 0652 0820 0945

Sampling Time -Stop Military 0802 0930 1054

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.90 -0.90 -0.90

Barometric Pressure Inches Mercury 30.26 30.26 30.26

Meter Correction Factor dimensionless 1.0110 1.0110 1.0110

Oxygen Concentration Mole Percent O2 6.5 6.0 6.0

Carbon Dioxide Concentration Mole Percent CO2 12.0 12.0 12.5

Volume of Gas Metered Actual Cubic Feet 35.208 35.980 35.953

Volume of Water Collected Milliliters 71 73 78

Sampling Time Minutes 64.00 64.00 64.00

Nozzle Diameter Inches 0.220 0.220 0.220

Weight of Solids Collected Milligrams 8.8 11.2 10.8

Area of Stack Square Feet 89.168 89.168 89.168

Avg. Sqr. Root Velocity Pressure Inches Water 0.8416 0.8479 0.8456

Average Orifice Pressure (H) Inches Water 1.2 1.2 1.2

Average Stack Temperature Degrees F 284 285 287

Average Meter Temperature Degrees F 54 54 53

3 Runs

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 37.091 37.909 37.954 37.651

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.17 29.15 29.16 29.16

Water vapor in Stack Gas Percent 8.3 8.3 8.8 8.5

Average Stack Gas Velocity Feet per second 55.5 56.0 55.9 55.8

Stack Gas Flow Rate Actual Cubic 297,057 299,744 299,149 298,650

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 212,777 214,206 213,361 213,448

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 195,190 196,404 194,541 195,378

 Feet Per Minute

Particulate Concentration Grains per Standard 0.0037 0.0045 0.0044 0.0042

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0024 0.0030 0.0028 0.0027

 Cubic Foot

Particulate Emission Rate Pounds per Hour 6.1 7.7 7.3 7.0

Particulate Emission Rate Pounds per Million 0.007 0.009 0.009 0.008

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 825 859 851 845

Isokinetic Rate Percent 100.3 101.8 102.9 101.7

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 4

STEADY STATE OPERATIONS
ATTACHMENT 3 - Crist Report 3 Test Results

2005 SO2 Emissions Test (Based on RATA Test)

Run 

Number Start Time/Date Stop Time/Date

Average 

Emissions 

(lbs/mmBTU 

SO2)

1 4/18/2005 16:36 4/18/2005 16:57 1.159

2 4/18/2005 17:22 4/18/2005 17:43 1.129

3 4/18/2005 18:08 4/18/2005 18:29 1.103

4 4/18/2005 18:54 4/18/2005 19:15 1.108

5 4/18/2005 19:40 4/18/2005 20:01 1.145

6 4/18/2005 20:26 4/18/2005 20:47 1.126

7 4/19/2005 10:49 4/19/2005 11:10 1.161

8 4/19/2005 11:35 4/19/2005 11:56 1.154

9 4/19/2005 12:21 4/19/2005 12:42 1.11

10 4/19/2005 13:11 4/19/2005 13:32 1.051

11 4/19/2005 13:57 4/19/2005 14:18 0.907

12 4/19/2005 14:43 4/19/2005 15:04 0.997

Avg 1.108

Crist Unit 4 High Load ~ 80 MWs

Runs 5, 6, and 11 not used
ATTACHMENT 4- Crist Report 4 Test Results

2005 SO2 Emissions Test (Based on RATA Test)

Run 

Number Start Time/Date Stop Time/Date

Average 

Emissions 

(lbs/mmBTU 

SO2)

1 1/25/2005 9:28 1/25/2005 9:49 0.855

2 1/25/2005 10:19 1/25/2005 10:40 0.875

3 1/25/2005 11:05 1/25/2005 11:26 0.824

4 1/25/2005 11:51 1/25/2005 12:12 0.818

5 1/25/2005 12:37 1/25/2005 12:58 0.827

6 1/25/2005 13:23 1/25/2005 13:44 0.83

7 1/26/2005 8:24 1/26/2005 8:45 0.844

8 1/26/2005 9:10 1/26/2005 9:31 0.829

9 1/26/2005 9:56 1/26/2005 10:17 0.838

10 1/26/2005 10:42 1/26/2005 11:03 0.849

Average: 0.839

Crist Unit 5 High Load ~80 MWs

Run 2 not used
ATTACHMENT 5 - Crist Report 5 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/25/2005 1/25/2005 1/25/2005

Sampling Time -Start Military 0727 0902 1022

Sampling Time -Stop Military 0837 1012 1134

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -1.00 -1.00 -1.00

Barometric Pressure Inches Mercury 30.30 30.30 30.30

Meter Correction Factor dimensionless 1.0110 1.0110 1.0110

Oxygen Concentration Mole Percent O2 7.5 6.5 6.5

Carbon Dioxide Concentration Mole Percent CO2 12.5 12.5 13.0

Volume of Gas Metered Actual Cubic Feet 37.705 37.014 37.995

Volume of Water Collected Milliliters 70 73 75

Sampling Time Minutes 64.00 64.00 64.00

Nozzle Diameter Inches 0.240 0.240 0.240

Weight of Solids Collected Milligrams 2.4 5.7 9.7

Area of Stack Square Feet 92.135 92.135 92.135

Avg. Sqr. Root Velocity Pressure Inches Water 0.7442 0.7555 0.7609

Average Orifice Pressure (H) Inches Water 1.273 1.3 1.4

Average Stack Temperature Degrees F 271.94 275.9 278.2

Average Meter Temperature Degrees F 46.88 55.2 62.3

3 Runs

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 40.347 38.971 39.462 39.593

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.37 29.27 29.33 29.32

Water vapor in Stack Gas Percent 7.5 8.1 8.2 8.0

Average Stack Gas Velocity Feet per second 48.5 49.5 49.9 49.3

Stack Gas Flow Rate Actual Cubic 268,200 273,493 275,607 272,433

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 195,420 198,210 199,107 197,579

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 180,666 182,149 182,758 181,858

 Feet Per Minute

Particulate Concentration Grains per Standard 0.0009 0.0023 0.0038 0.0023

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0006 0.0015 0.0025 0.0015

 Cubic Foot

Particulate Emission Rate Pounds per Hour 1.4 3.5 5.9 3.6

Particulate Emission Rate Pounds per Million 0.002 0.005 0.008 0.005

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 711 770 773 751

Isokinetic Rate Percent 102.3 98.0 98.9 99.8

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 5

SOOT BLOWING OPERATIONS
ATTACHMENT 6 - Crist Report 6 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/26/2005 1/26/2005 1/26/2005

Sampling Time -Start Military 0832 0957 1120

Sampling Time -Stop Military 0942 1107 1228

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -1.00 -1.00 -1.00

Barometric Pressure Inches Mercury 30.30 30.30 30.30

Meter Correction Factor dimensionless 1.0110 1.0110 1.0110

Oxygen Concentration Mole Percent O2 6.0 6.0 6.5

Carbon Dioxide Concentration Mole Percent CO2 13.0 12.5 12.5

Volume of Gas Metered Actual Cubic Feet 37.305 37.920 38.187

Volume of Water Collected Milliliters 64 73 71

Sampling Time Minutes 64.00 64.00 64.00

Nozzle Diameter Inches 0.240 0.240 0.240

Weight of Solids Collected Milligrams 3.4 5.8 8.5

Area of Stack Square Feet 92.135 92.135 92.135

Avg. Sqr. Root Velocity Pressure Inches Water 0.7443 0.7520 0.7428

Average Orifice Pressure (H) Inches Water 1.3 1.3 1.3

Average Stack Temperature Degrees F 285 290 292

Average Meter Temperature Degrees F 72 79 81

3 Runs

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 38.053 38.153 38.324 38.177

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.42 29.23 29.28 29.31

Water vapor in Stack Gas Percent 7.3 8.3 8.0 7.9

Average Stack Gas Velocity Feet per second 48.9 49.7 49.2 49.3

Stack Gas Flow Rate Actual Cubic 270,438 274,960 271,837 272,412

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 193,570 195,575 192,696 193,947

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 179,370 179,417 177,240 178,675

 Feet Per Minute

Particulate Concentration Grains per Standard 0.0014 0.0023 0.0034 0.0024

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0009 0.0015 0.0022 0.0016

 Cubic Foot

Particulate Emission Rate Pounds per Hour 2.1 3.6 5.2 3.6

Particulate Emission Rate Pounds per Million 0.003 0.005 0.007 0.005

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 785 785 749 773

Isokinetic Rate Percent 97.2 97.4 99.1 97.9

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 5

STEADY STATE OPERATIONS
ATTACHMENT 7 - Crist Report 7 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 3/8/2005 3/8/2005 3/8/2005

Sampling Time -Start Military 0640 0800 0910

Sampling Time -Stop Military 0742 0902 1010

Oxygen F Factor SDCF/MMBTU 9780 9780 9780

Stack Static Pressure Inches Water -1.00 -1.00 -1.00

Barometric Pressure Inches Mercury 30.00 30.00 30.00

Meter Correction Factor dimensionless 1.011 1.011 1.011

Oxygen Concentration Mole Percent O2 5.5 5.0 5.0

Carbon Dioxide Concentration Mole Percent CO2 12.0 11.0 12.0

Volume of Gas Metered Actual Cubic Feet 38.195 36.800 37.185

Volume of Water Collected Milliliters 59.00 63.0 63.0

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.215 0.215 0.215

Weight of Solids Collected Milligrams 8.9 8.9 18.2

Number of Points Sampled 30 30 30

Area of Stack Square Feet 270.0000 270.0000 270.0000

Avg. Sqr. Root Velocity Pressure Inches Water 1.1002 1.0842 1.1003

Average Stack Temperature Degrees F 333.6 339.5 336.6

Average Meter Temperature Degrees F 55.3 56.8 49.2

3 Runs

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 39.832 38.264 39.246 39.114

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.349 29.100 29.269 29.239

Water vapor in Stack Gas Percent 6.5176 7.2 7.0 6.9

Average Stack Gas Velocity Feet per second 75.09 74.59 75.33 75.00

Stack Gas Flow Rate Actual Cubic 1,216,442 1,208,323 1,220,387 1,215,051

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 809,298 797,962 808,931 805,397

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 756,551 740,569 752,103 749,741

 Feet Per Minute

Stack Gas Flow Rate Pounds Dry Air 3,413,523 3,341,416 3,393,457 3,382,799

 per Hour

Particulate Concentration Grains per Standard 0.00344 0.00358 0.00714 0.00472

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.00214 0.00220 0.00440 0.00291

 Cubic Foot

Particulate Emission Rate Pounds per Hour 22.31 22.74 46.04 30.36

Particulate Emission Rate Pounds per Million 0.00652 0.00658 0.01312 0.00874

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 3,420 3,456 3,510 3,462

Isokinetic Rate Percent 94.0 92.2 93.1 93.1

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 6

SOOT BLOWING OPERATIONS
ATTACHMENT 8 - Crist Report 8 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 3/9/2005 3/9/2005 3/9/2005

Sampling Time -Start Military 0654 0824 0935

Sampling Time -Stop Military 0756 0928 1039

Oxygen F Factor SDCF/MMBTU 9780 9780 9780

Stack Static Pressure Inches Water -1.20 -1.20 -1.20

Barometric Pressure Inches Mercury 30.10 30.10 30.10

Meter Correction Factor dimensionless 1.011 1.011 1.011

Oxygen Concentration Mole Percent O2 5.5 5.5 5.5

Carbon Dioxide Concentration Mole Percent CO2 12.5 13.0 13.0

Volume of Gas Metered Actual Cubic Feet 41.127 39.149 39.895

Volume of Water Collected Milliliters 61.00 65.0 71.0

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.215 0.215 0.215

Weight of Solids Collected Milligrams 17.3 12.1 16.2

Number of Points Sampled 30 30 30

Area of Stack Square Feet 270.0000 270.0000 270.0000

Avg. Sqr. Root Velocity Pressure Inches Water 1.0866 1.0957 1.1038

Average Orifice Pressure (H) Inches Water 1.7 1.7 1.7

Average Stack Temperature Degrees F 335.1 335.2 338.3

Average Meter Temperature Degrees F 51.3 54.3 56.6

3 Runs

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 43.392 41.056 41.658 42.035

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.462 29.447 29.387 29.432

Water vapor in Stack Gas Percent 6.2 6.9 7.4 6.9

Average Stack Gas Velocity Feet per second 73.98 74.62 75.39 74.67

Stack Gas Flow Rate Actual Cubic 1,198,455 1,208,901 1,221,363 1,209,573

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 798,095 804,950 810,156 804,400

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 748,562 749,124 749,989 749,225

 Feet Per Minute

Stack Gas Flow Rate Pounds Dry Air 3,377,480 3,380,013 3,383,917 3,380,470

 per Hour

Particulate Concentration Grains per Standard 0.00614 0.00454 0.00599 0.00556

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.00383 0.00281 0.00368 0.00344

 Cubic Foot

Particulate Emission Rate Pounds per Hour 39.39 29.14 38.50 35.68

Particulate Emission Rate Pounds per Million 0.01164 0.00861 0.01136 0.01053

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 3,384 3,386 3,390 3,387

Isokinetic Rate Percent 103.4 97.8 99.1 100.1

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 6

STEADY STATE OPERATIONS
ATTACHMENT 9 - Crist Report 9 Test Results

2005 SO2 Emissions Test (Based on RATA Test)

Run 

Number Start Time/Date Stop Time/Date

Average 

Emissions 

(lbs/mmBTU 

SO2)

1 3/17/2005 8:54 3/17/2005 9:15 1.176

2 3/17/2005 9:40 3/17/2005 10:01 1.116

3 3/17/2005 10:26 3/17/2005 10:47 1.108

4 3/17/2005 11:12 3/17/2005 11:33 1.103

5 3/17/2005 11:58 3/17/2005 12:19 1.073

6 3/17/2005 12:44 3/17/2005 13:05 1.056

7 3/17/2005 13:30 3/17/2005 13:51 1.031

8 3/17/2005 14:22 3/17/2005 14:43 1.039

9 3/17/2005 15:08 3/17/2005 15:29 1.026

Average: 1.081

Crist Unit 6 High Load ~315 MWs
ATTACHMENT 10 - Crist Report 10 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 6/28/2005 6/28/2005 6/28/2005

Sampling Time -Start Military 1414 1532 1652

Sampling Time -Stop Military 1518 1639 1758

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.80 0.80 0.80

Barometric Pressure Inches Mercury 30.10 30.10 30.10

Meter Correction Factor dimensionless 0.999 0.999 0.999

Oxygen Concentration Mole Percent O2 8.0 8.0 8.0

Carbon Dioxide Concentration Mole Percent CO2 11.0 11.0 11.0

Volume of Gas Metered Actual Cubic Feet 35.380 36.326 35.973

Volume of Water Collected Milliliters 39.00 42.00 46.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.205 0.205 0.205

Weight of Solids Collected Milligrams 6.0 12.8 6.6

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 0.9304 0.9512 0.9368

Average Orifice Pressure (H) Inches Water 1.2 1.3 1.2

Average Stack Temperature Degrees F 286 290 290

Average Meter Temperature Degrees F 88 88 86

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 34.400 35.289 35.075 34.922

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.47 29.44 29.38 29.43

Water vapor in Stack Gas Percent 5.1 5.3 5.8 5.4

Average Stack Gas Velocity Feet per second 61.2 62.8 61.9 62.0

Stack Gas Flow Rate Actual Cubic 1,344,519 1,379,554 1,360,231 1,361,435

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 959,638 978,560 964,596 967,598

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 911,022 926,648 908,512 915,394

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 68,236 69,406 68,048 68,563

Per Minute

Particulate Concentration Grains per Standard 0.0027 0.0056 0.0029 0.0037

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0018 0.0038 0.0019 0.0025

 Cubic Foot

Particulate Emission Rate Pounds per Hour 21.0 44.4 22.6 29.3

Particulate Emission Rate Pounds per Million 0.006 0.013 0.007 0.008

 Btu (O2 F Factor)

Allowable Particulate Emission Rate Pounds per Million 0.1 0.1 0.1 0.1

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 3,450 3,509 3,440 3,466

Isokinetic Rate Percent 100.5 101.4 102.8 101.6

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 7
ATTACHMENT 11 - Crist Report 11 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 6/29/2005 6/29/2005 6/29/2005

Sampling Time -Start Military 0649 0814 0934

Sampling Time -Stop Military 0756 0921 1041

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.80 0.80 0.80

Barometric Pressure Inches Mercury 30.05 30.05 30.05

Meter Correction Factor dimensionless 0.999 0.999 0.999

Oxygen Concentration Mole Percent O2 8.0 7.5 7.5

Carbon Dioxide Concentration Mole Percent CO2 11.0 11.5 11.0

Volume of Gas Metered Actual Cubic Feet 36.130 36.484 36.218

Volume of Water Collected Milliliters 58.00 48.00 44.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.205 0.205 0.205

Weight of Solids Collected Milligrams 10.5 16.8 14.0

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 0.9455 0.9584 0.9397

Average Orifice Pressure (H) Inches Water 1.3 1.3 1.3

Average Stack Temperature Degrees F 295 296 294

Average Meter Temperature Degrees F 90 95 97

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 34.906 34.931 34.562 34.800

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.20 29.40 29.38 29.33

Water vapor in Stack Gas Percent 7.3 6.1 5.7 6.3

Average Stack Gas Velocity Feet per second 62.9 63.6 62.3 62.9

Stack Gas Flow Rate Actual Cubic 1,382,339 1,397,362 1,369,062 1,382,921

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 972,640 981,866 964,363 972,956

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 902,086 922,217 909,842 911,382

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 67,566 69,074 68,147 68,262

Per Minute

Particulate Concentration Grains per Standard 0.0046 0.0074 0.0062 0.0061

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0030 0.0049 0.0041 0.0040

 Cubic Foot

Particulate Emission Rate Pounds per Hour 35.8 58.5 48.6 47.7

Particulate Emission Rate Pounds per Million 0.010 0.016 0.014 0.013

 Btu (O2 F Factor)

Allowable Particulate Emission Rate Pounds per Million 0.3 0.3 0.3 0.3

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 3,416 3,627 3,579 3,541

Isokinetic Rate Percent 103.0 100.9 101.1 101.7

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 7 - SOOT BLOWING
ATTACHMENT 12 - Crist Report 12 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 9/22/2005 9/22/2005 9/22/2005

Sampling Time -Start Military 0656 0841 1018

Sampling Time -Stop Military 0801 0946 1123

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.50 1.50 1.50

Barometric Pressure Inches Mercury 29.92 29.92 29.92

Meter Correction Factor dimensionless 0.988 0.988 0.988

Oxygen Concentration Mole Percent O2 7.5 7.0 7.0

Carbon Dioxide Concentration Mole Percent CO2 11.0 11.5 11.5

Volume of Gas Metered Actual Cubic Feet 38.000 37.141 38.013

Volume of Water Collected Milliliters 55.00 65.00 71.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.180 0.180 0.180

Weight of Solids Collected Milligrams 25.1 6.7 6.6

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3555 1.3400 1.3610

Average Orifice Pressure (H) Inches Water 1.8 1.8 1.9

Average Stack Temperature Degrees F 321 326 328

Average Meter Temperature Degrees F 82 86 91

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 36.716 35.683 36.188 36.196

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.27 29.16 29.10 29.17

Water vapor in Stack Gas Percent 6.6 7.9 8.5 7.6

Average Stack Gas Velocity Feet per second 91.8 91.1 92.8 91.9

Stack Gas Flow Rate Actual Cubic 2,016,372 2,002,888 2,039,915 2,019,725

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,367,579 1,350,191 1,370,790 1,362,853

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,277,502 1,243,565 1,254,900 1,258,656

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 95,685 93,143 93,992 94,273

Per Minute

Particulate Concentration Grains per Standard 0.0105 0.0029 0.0028 0.0054

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0067 0.0018 0.0017 0.0034

 Cubic Foot

Particulate Emission Rate Pounds per Hour 115.3 30.8 30.2 58.8

Particulate Emission Rate Pounds per Million 0.023 0.006 0.006 0.012

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 5,025 5,074 5,120 5,073

Isokinetic Rate Percent 99.3 99.1 99.6 99.3

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

SOOT BLOWING OPERATIONS
ATTACHMENT 13 - Crist Report 13 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 9/23/2005 9/23/2005 9/23/2005

Sampling Time -Start Military 0646 0815 0928

Sampling Time -Stop Military 0753 0920 1032

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.50 1.50 1.50

Barometric Pressure Inches Mercury 29.89 29.89 29.89

Meter Correction Factor dimensionless 0.988 0.988 0.988

Oxygen Concentration Mole Percent O2 7.0 7.5 7.0

Carbon Dioxide Concentration Mole Percent CO2 12.0 11.0 1.5

Volume of Gas Metered Actual Cubic Feet 37.120 37.370 37.067

Volume of Water Collected Milliliters 73.00 70.00 69.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.180 0.180 0.180

Weight of Solids Collected Milligrams 5.2 7.3 6.3

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3446 1.3642 1.3442

Average Orifice Pressure (H) Inches Water 1.8 1.9 1.8

Average Stack Temperature Degrees F 325 329 329

Average Meter Temperature Degrees F 80 82 86

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 35.986 36.078 35.551 35.872

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.14 29.05 27.64 28.61

Water vapor in Stack Gas Percent 8.7 8.4 8.4 8.5

Average Stack Gas Velocity Feet per second 91.5 93.2 94.1 92.9

Stack Gas Flow Rate Actual Cubic 2,011,033 2,047,292 2,068,412 2,042,246

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,355,190 1,374,315 1,388,198 1,372,568

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,237,068 1,259,307 1,271,994 1,256,123

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 92,656 94,322 95,272 94,084

Per Minute

Particulate Concentration Grains per Standard 0.0022 0.0031 0.0027 0.0027

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0014 0.0019 0.0017 0.0017

 Cubic Foot

Particulate Emission Rate Pounds per Hour 23.6 33.6 29.8 29.0

Particulate Emission Rate Pounds per Million 0.005 0.007 0.006 0.006

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 5,047 4,953 5,190 5,064

Isokinetic Rate Percent 100.5 98.9 96.5 98.6

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

STEADY STATE OPERATIONS
ATTACHMENT 14 - Crist Report 14 Test Results

2005 SO2 Emissions Test (Based on RATA Test)

Run Number Start Time Date Stop Time Date

Average 

Emissions 

(lbs/mmBTU 

SO2)

1 9/27/2005 16:05 9/27/2005 16:26 0.904

2 9/27/2005 17:16 9/27/2005 17:37 0.900

3 9/27/2005 18:07 9/27/2005 18:28 0.907

4 9/27/2005 18:58 9/27/2005 19:19 0.897

5 9/27/2005 19:49 9/27/2005 20:10 0.897

6 9/27/2005 20:40 9/27/2005 21:01 0.906

7 9/27/2005 21:31 9/27/2005 21:52 0.905

8 9/27/2005 22:22 9/27/2005 22:43 0.896

9 9/27/2005 23:13 9/27/2005 23:34 0.899

10 9/28/2005 0:04 9/28/2005 0:25 0.889

9/28/2005 0:55 9/28/2005 1:16 0.897

11 9/28/2005 1:46 9/28/2005 2:07 0.905

Average 0.90

Crist Unit 7 High Load ~ 500 MW
ATTACHMENT 15 - Crist Report 15 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 12/6/2005 12/6/2005 12/6/2005

Sampling Time -Start Military 0706 0827 0945

Sampling Time -Stop Military 0813 0931 1049

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.50 1.50 1.50

Barometric Pressure Inches Mercury 30.30 30.30 30.30

Meter Correction Factor dimensionless 0.988 0.988 0.988

Oxygen Concentration Mole Percent O2 8.0 8.0 7.5

Carbon Dioxide Concentration Mole Percent CO2 12.0 11.5 11.5

Volume of Gas Metered Actual Cubic Feet 35.382 36.215 37.460

Volume of Water Collected Milliliters 76.00 73.00 68.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.185 0.185 0.185

Weight of Solids Collected Milligrams 32.9 30.0 24.4

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3255 1.2997 1.3310

Average Orifice Pressure (H) Inches Water 2.0 1.9 2.0

Average Stack Temperature Degrees F 293 294 298

Average Meter Temperature Degrees F 61 63 68

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 36.054 36.732 37.678 36.821

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.14 29.12 29.19 29.15

Water vapor in Stack Gas Percent 9.0 8.6 7.8 8.5

Average Stack Gas Velocity Feet per second 87.7 86.1 88.3 87.4

Stack Gas Flow Rate Actual Cubic 1,928,239 1,892,427 1,940,637 1,920,434

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,373,667 1,346,307 1,373,620 1,364,531

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,249,672 1,231,138 1,266,067 1,248,959

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 93,600 92,212 94,828 93,547

Per Minute

Particulate Concentration Grains per Standard 0.0141 0.0126 0.0100 0.0122

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0091 0.0082 0.0065 0.0079

 Cubic Foot

Particulate Emission Rate Pounds per Hour 150.5 132.7 108.2 130.5

Particulate Emission Rate Pounds per Million 0.032 0.028 0.022 0.027

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 4,732 4,662 4,980 4,791

Isokinetic Rate Percent 94.3 97.5 97.3 96.4

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

STEADY STATE
ATTACHMENT 16 - Crist Report 16 Test Results

Plant Load Indicator\Label

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/31/2006 5/31/2006 5/31/2006

Sampling Time -Start Military 0632 0756 0914

Sampling Time -Stop Military 0743 0906 1025

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.85 -0.85 -0.85

Barometric Pressure Inches Mercury 30.17 30.17 30.17

Standard Orifice Pressure H@ Inches Water 2.31 2.31 2.31

Meter Correction Factor dimensionless 0.976 0.976 0.976

Oxygen Concentration Mole Percent O2 7.20 7.40 7.40

Carbon Dioxide Concentration Mole Percent CO2 11.00 11.50 11.00

Volume of Gas Metered Actual Cubic Feet 38.335 37.350 36.216

Volume of Water Collected Milliliters 70.00 80.00 76.00

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.218 0.220 0.218

Weight of Solids Collected Milligrams 16.3 16.4 11.0

Area of Stack Square Feet 89.169 89.169 89.169

Avg. Sqr. Root Velocity Pressure Inches Water 0.8328 0.8383 0.8366

Average Orifice Pressure (H) Inches Water 1.3889 1.4593 1.1543

Average Stack Temperature Degrees F 300 288 289

Average Meter Temperature Degrees F 74 73 73

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 37.412 36.555 35.415 36.461

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.05 30.14 30.06 30.08

Water vapor in Stack Gas Percent 8.1 9.3 9.2 8.9

Average Stack Gas Velocity Feet per second 55.7 55.7 55.7 55.7

Stack Gas Flow Rate Actual Cubic 297,997 298,126 297,950 298,024

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 208,398 211,593 211,238 210,410

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,530 191,832 191,858 191,740

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,346 14,368 14,370 14,361

Per Minute

Particulate Concentration Grains per Standard 0.0067 0.0069 0.0048 0.0061

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0043 0.0044 0.0031 0.0039

 Cubic Foot

Particulate Emission Rate Pounds per Hour 11.0 11.4 7.9 10.1

Particulate Emission Rate Pounds per Million 0.014 0.015 0.010 0.013

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 770 760 760 764

Isokinetic Rate Percent 105.0 100.6 99.2 101.6

Post Test Meter Correction Factor dimensionless 0.95 1.00 0.92 0.96

Percent Difference Allowed 5% -2.19 2.49 -5.63 -1.78

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

 PLANT CRIST UNIT 4, SOOT BLOWING

5/31/2006
ATTACHMENT 17 - Crist Report 17 Test Results

Plant Load Indicator\Label

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/31/2006 5/31/2006 5/31/2006

Sampling Time -Start Military 1230 1415 1532

Sampling Time -Stop Military 1339 1522 1641

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.85 -0.85 -0.85

Barometric Pressure Inches Mercury 30.17 30.17 30.17

Standard Orifice Pressure H@ Inches Water 2.31 2.31 2.31

Meter Correction Factor dimensionless 0.976 0.976 0.976

Oxygen Concentration Mole Percent O2 6.80 6.50 7.00

Carbon Dioxide Concentration Mole Percent CO2 11.50 12.00 12.00

Volume of Gas Metered Actual Cubic Feet 34.400 33.800 38.065

Volume of Water Collected Milliliters 67.00 66.00 77.00

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.208 0.212 0.218

Weight of Solids Collected Milligrams 12.1 10.4 15.8

Area of Stack Square Feet 89.169 89.169 89.169

Avg. Sqr. Root Velocity Pressure Inches Water 0.8644 0.8229 0.8575

Average Orifice Pressure (H) Inches Water 1.1938 1.1557 1.4229

Average Stack Temperature Degrees F 294 292 296

Average Meter Temperature Degrees F 73 72 72

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 33.642 33.109 37.317 34.689

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.11 30.18 30.20 30.16

Water vapor in Stack Gas Percent 8.6 8.6 8.9 8.7

Average Stack Gas Velocity Feet per second 57.6 54.7 57.2 56.5

Stack Gas Flow Rate Actual Cubic 308,074 292,632 305,796 302,167

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 217,145 206,775 214,987 212,969

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 198,534 189,038 195,955 194,509

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,870 14,159 14,677 14,569

Per Minute

Particulate Concentration Grains per Standard 0.0055 0.0048 0.0065 0.0056

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0036 0.0031 0.0042 0.0036

 Cubic Foot

Particulate Emission Rate Pounds per Hour 9.4 7.8 11.0 9.4

Particulate Emission Rate Pounds per Million 0.011 0.010 0.014 0.012

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 822 799 800 807

Isokinetic Rate Percent 100.0 99.5 102.3 100.6

Post Test Meter Correction Factor dimensionless 0.98 0.98 0.97 0.98

Percent Difference Allowed 5% 0.77 0.71 -0.80 0.23

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

 PLANT CRIST UNIT 4 STEADY STATE

5/31/2006
ATTACHMENT 18 - Crist Report 18 Test Results

Urea

Flowrate Carbon Carbon Sulfur Nitrogen

Water (Pounds Per Heat Power F Factor Oxygen Oxygen Dioxide Dioxide Sulfur Sulfur Dioxide Nitrogen Nitrogen Oxides

Start Stop Vapor in Hour) Input Generation Carbon Dioxide ( Dry) ( Wet) ( Dry) ( Wet) Dioxide Dioxide Emissions Oxides Oxides Emissions

TEST Time Time Stack Gas (measured) ( Dry) (measured) (calculated) (measured) (calculated) Emissions Emissions (CO2 F factor) Emissions Emissions (CO2 F factor)

Military Military (Percent) (MMbtu/Hour) (MegaWatts) (SDCF/MMbtu) (Percent) (Percent) (Percent) (Percent) (ppm-dry) (ppm-wet) (Lbs/MMbtu) (ppm-dry) (ppm-wet) (Lbs/MMbtu)

RUN 1 Urea On 11:40 12:01 8.2 414.87 773.35 80 1,800 6.8 6.3 12.7 11.7 399.2 366.5 0.939 142.4 130.7 0.240

RUN 2 Urea On 12:09 12:30 8.2 413.89 774.56 79 1,800 6.7 6.2 12.9 11.9 376.5 345.7 0.872 144.8 132.9 0.241

RUN 3 Urea On 12:36 12:57 8.2 414.14 774.18 79 1,800 6.7 6.2 12.7 11.7 388.8 356.9 0.915 142.9 131.2 0.241

RUN 4 Urea On 13:03 13:24 9.3 414.65 781.08 79 1,800 6.6 6.0 12.9 11.7 386.4 350.5 0.897 143.2 129.9 0.239

RUN 5 Urea On 13:31 13:52 9.3 415.60 784.13 79 1,800 6.6 6.0 12.9 11.7 402.1 364.7 0.937 141.8 128.6 0.237

RUN 6 Urea On 14:00 14:21 9.3 415.39 765.66 79 1,800 6.6 6.0 12.9 11.7 403.2 365.7 0.940 142.7 129.5 0.239

RUN 7 Urea On 14:29 14:50 9.1 415.49 765.69 79 1,800 6.6 6.0 12.8 11.6 406.0 369.0 0.951 142.7 129.7 0.240

RUN 8 Urea On 14:57 15:18 9.1 414.32 772.80 79 1,800 6.6 6.0 12.9 11.7 418.1 379.9 0.971 142.6 129.6 0.238

RUN 9 Urea On 15:25 15:46 9.1 415.06 770.72 79 1,800 6.7 6.1 12.8 11.6 425.7 386.9 1.000 143.4 130.3 0.242

Average 8.9 414.82 773.57 79 1,800 6.7 6.1 12.8 11.7 400.7 365.1 0.936 143.0 130.3 0.240

Carbon Nitrogen

Heat Power F Factor Dioxide Nitrogen Oxides

Start Stop Input Generation Carbon Dioxide ( Dry) Oxides Emissions Average NOX Emissions Uncontrolled (lbs/mmbtu)= 0.353

TEST Time Time (measured) ( Dry) (measured) Emissions (CO2 F factor) Average NOX Emissions Controlled (lbs/mmbtu)= 0.240

Military Military (MMbtu/Hour) (MegaWatts) (SDCF/MMbtu) (Percent) (ppm-dry) (Lbs/MMbtu)

RUN 1 Urea Off 7:55 8:55 797.18 80 1,800 12.5 201.1 0.345

RUN 2 Urea Off 9:02 10:02 769.42 80 1,800 12.3 211.7 0.369 NOX Reduction Efficiency (%) = 32.2

RUN 3 Urea Off 10:11 11:11 777.84 80 1,800 12.6 202.1 0.346 Targeted Reduction Efficiency (%) = 25.0

Average 781.48 80 1,800 12.5 204.9 0.353

Note: Heat input limit from particulate testing is 888 MMBtu/Hr.

Note: Urea flow is for the 40% solution.

6/1/2006

TABLE I. SULFUR DIOIXDE, NITROGEN OXIDES, OXYGEN, AND CARBON DIOIXDE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 4
ATTACHMENT 19 - Crist Report 19 Test Results

2006 SO2 Emissions Test (Based on RATA Test)

Run Date Start Time Stop Time Heat Input mmbtu/hr MW SO2 lbm/mmbtu

1 6/1/2006 11:40 12:01 773.35 80 0.939

2 6/1/2006 12:09 12:30 774.56 79 0.872

3 6/1/2006 12:36 12:57 774.18 79 0.915

4 6/1/2006 13:03 13:24 781.08 79 0.897

5 6/1/2006 13:31 13:52 784.13 79 0.937

6 6/1/2006 14:00 14:21 765.66 79 0.94

7 6/1/2006 14:29 14:50 765.69 79 0.951

8 6/1/2006 14:57 15:18 772.8 79 0.971

9 6/1/2006 15:25 15:46 770.72 79 1.000

0.936

Crist Unit 4
ATTACHMENT 20 - Crist Report 20 Test Results

Title of Run RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Date Month/Day/Year 9/21/2006 9/21/2006 9/21/2006 9/21/2006 9/21/2006 9/21/2006

Sampling Time -Start Military 0803 0938 1110 0803 0938 1110

Sampling Time -Stop Military 0903 1038 1210 0903 1038 1210

Number of Ports dimensionless 1 1 1 1 1 1

Number of Points per Port dimensionless 12 12 12 12 12 12

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.15 -0.15 -0.15 -0.15 -0.15 -0.15

Barometric Pressure Inches Mercury 30.10 30.10 30.10 30.10 30.10 30.10

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858 2.258 2.258 2.258

Meter Correction Factor dimensionless 0.978 0.978 0.978 0.982 0.982 0.982

Oxygen Concentration Mole Percent O2 7.0 7.0 7.0 7.0 7.0 7.0

Carbon Dioxide Concentration Mole Percent CO2 11 11 11 11 11 11

Volume of Gas Metered Actual Cubic Feet 40.055 41.000 37.660 35.692 36.580 36.031

Volume of Water Collected Milliliters 63 65 66 78 81 81

Sampling Time Minutes 60 60 60 60 60 60

Area of Stack Square Feet 89.169 89.169 89.169 89.169 89.169 89.169

Average Orifice Pressure (H) Inches Water 1.5 1.5 1.5 1.5 1.5 1.5

Average Stack Temperature Degrees F 294 295 301 294 295 300

Average Meter Temperature Degrees F 75 79 83 74 82 81

Final Volume of H2SO4 Solution Milliliters 74.00 60.00 42.00 162.00 178.00 168.00

Normality of Titrant (BaCl2) Equlivents/Liter 0.0991 0.0991 0.0991 0.0991 0.0991 0.0991

Volume of Aloquit (H2SO4) Milliliters 25.00 25.00 20.00 25.00 25.00 25.00

Volume of Titrant for H2SO4 Blank Milliliters 0.00 0.00 0.00 0.00 0.00 0.00

Volume of Titrant For H2SO4 Aloquit Milliliters 0.30 0.28 0.10 2.45 1.90 2.00

RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Volume of Gas Sampled Standard Dry 39.014 39.675 36.186 35.021 35.319 34.869

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.04 30.04 30.04 30.04 30.04 30.04

Water vapor in Stack Gas Percent 7.1 7.2 7.9 9.5 9.7 9.9

Stack Gas Flow Rate Actual Cubic 290,707 290,707 290,707 290,707 290,707 290,707

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 206,814 206,814 206,814 206,814 206,814 206,814

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,146 191,146 191,146 191,146 191,146 191,146

 Feet Per Minute

Heat Input (O2 F Factor) Million Btu per Hour 780 780 780 780 780 780

Post Test Meter Correction Factor dimensionless 0.99 0.97 1.06 1.01 0.99 1.01

Percent Difference Allowed 5% 1.6 -0.3 8.7 2.9 1.2 2.6

Concentration of Sulfuric Acid Grains per Standard 0.002 0.001 0.000 0.034 0.029 0.029

 Dry Cubic Foot

Sulfuric Acid Emission Rate Pounds per Hour 2.796 2.044 0.713 55.696 47.059 47.356

Sulfuric Acid Emission Rate PPM 0.958 0.700 0.244 19.078 16.120 16.222

Calculations

TABLE I. SULFURIC ACID MIST EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 4
ATTACHMENT 21 - Crist Report 21 Test Results

2006 SO2 Emissions Test (Based on RATA Test) 

Crist Unit 5

Run Time Time Unit RM-6C (SO2)

Number Started Stopped Load lbs/mmBtu

1 1/24/06 7:27 1/24/06 7:48 79 0.838

2 1/24/06 8:11 1/24/06 8:32 79 0.838

3 1/24/06 8:56 1/24/06 9:17 79 0.829

4 1/24/06 9:46 1/24/06 10:07 80 0.834

5 1/24/06 10:30 1/24/06 10:51 80 0.839

6 1/24/06 11:14 1/24/06 11:35 80 0.840

7 1/24/06 11:58 1/24/06 12:19 76 0.840

8 1/24/06 12:42 1/24/06 13:03 80 0.836

9 1/24/06 13:24 1/24/06 13:45 81 0.840

0.837
ATTACHMENT 22 - Crist Report 22 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/24/2006 1/24/2006 1/24/2006

Sampling Time -Start Military 0731 0909 1030

Sampling Time -Stop Military 0840 1017 1138

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.90 -0.90 -0.90

Barometric Pressure Inches Mercury 30.35 30.35 30.35

Meter Correction Factor dimensionless 0.9880 0.9880 0.9880

Oxygen Concentration Mole Percent O2 7.0 7.5 7.5

Carbon Dioxide Concentration Mole Percent CO2 12.0 12.0 12.0

Volume of Gas Metered Actual Cubic Feet 39.655 40.708 40.375

Volume of Water Collected Milliliters 65 62 63

Sampling Time Minutes 64.00 64.00 64.00

Nozzle Diameter Inches 0.235 0.235 0.235

Weight of Solids Collected Milligrams 22.6 19.3 26.4

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8165 0.8281 0.8173

Average Orifice Pressure (H) Inches Water 1.693 1.8 1.8

Average Stack Temperature Degrees F 296.72 297.3 297.7

Average Meter Temperature Degrees F 57.50 57.0 55.9

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 40.725 41.860 41.598 41.394

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.35 29.42 29.41 29.39

Water vapor in Stack Gas Percent 7.0 6.5 6.7 6.7

Average Stack Gas Velocity Feet per second 54.1 54.8 54.1 54.3

Stack Gas Flow Rate Actual Cubic 289,352 293,182 289,528 290,687

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 204,311 206,845 204,174 205,110

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 190,034 193,364 190,588 191,329

 Feet Per Minute

Particulate Concentration Grains per Standard 0.0085 0.0071 0.0098 0.0085

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0056 0.0047 0.0064 0.0056

 Cubic Foot

Particulate Emission Rate Pounds per Hour 13.9 11.8 16.0 13.9

Particulate Emission Rate Pounds per Million 0.018 0.015 0.021 0.018

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 775 761 750 762

Isokinetic Rate Percent 99.1 100.1 100.9 100.0

Calculations

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 5

SOOT BLOWING OPERATIONS
ATTACHMENT 23 - Crist Report 23 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/25/2006 1/25/2006 1/25/2006

Sampling Time -Start Military 0656 0818 0950

Sampling Time -Stop Military 0804 0926 1058

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.75 -0.75 -0.75

Barometric Pressure Inches Mercury 30.30 30.30 30.30

Meter Correction Factor dimensionless 0.9880 0.9880 0.9880

Oxygen Concentration Mole Percent O2 7.5 7.0 7.5

Carbon Dioxide Concentration Mole Percent CO2 11.5 12.0 12.5

Volume of Gas Metered Actual Cubic Feet 40.914 40.913 41.042

Volume of Water Collected Milliliters 72 77 72

Sampling Time Minutes 64.00 64.00 64.00

Nozzle Diameter Inches 0.235 0.235 0.235

Weight of Solids Collected Milligrams 41.1 50.6 52.9

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8182 0.8212 0.8285

Average Orifice Pressure (H) Inches Water 1.8 1.8 1.8

Average Stack Temperature Degrees F 287 290 293

Average Meter Temperature Degrees F 51 54 57

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 42.511 42.270 42.122 42.301

 Cubic Feet 

Molecular Wt. of Stack Gas LB/LB-MOLE 29.24 29.24 29.38 29.29

Water vapor in Stack Gas Percent 7.4 7.9 7.4 7.6

Average Stack Gas Velocity Feet per second 54.0 54.3 54.8 54.3

Stack Gas Flow Rate Actual Cubic 288,691 290,492 292,937 290,707

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 206,318 206,602 207,520 206,814

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,085 190,287 192,067 191,146

 Feet Per Minute

Particulate Concentration Grains per Standard 0.0149 0.0184 0.0193 0.0176

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0099 0.0121 0.0127 0.0115

 Cubic Foot

Particulate Emission Rate Pounds per Hour 24.4 30.1 31.8 28.8

Particulate Emission Rate Pounds per Million 0.032 0.039 0.042 0.038

Allowable Particulate Emission Rate Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 752 776 755 761

Isokinetic Rate Percent 102.9 102.7 101.4 102.3

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 5

STEADY STATE OPERATIONS
ATTACHMENT 24 - Crist Report 24 Test Results

Title of Run RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Date Month/Day/Year 9/20/2006 9/20/2006 9/20/2006 9/20/2006 9/20/2006 9/20/2006

Sampling Time -Start Military 0912 1042 1210 0912 1042 1210

Sampling Time -Stop Military 1012 1142 1310 1012 1142 1310

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.15 -0.15 -0.15 -0.15 -0.15 -0.15

Barometric Pressure Inches Mercury 30.00 30.00 30.00 30.07 30.07 30.07

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858 2.258 2.258 2.258

Meter Correction Factor dimensionless 0.978 0.978 0.978 0.982 0.982 0.982

Oxygen Concentration Mole Percent O2 7.0 7.0 7.0 7.0 7.0 7.0

Carbon Dioxide Concentration Mole Percent CO2 11 11 11 11 11 11

Volume of Gas Metered Actual Cubic Feet 40.770 40.915 41.000 35.950 36.955 36.795

Volume of Water Collected Milliliters 79 78 82 90 70 70

Sampling Time Minutes 60 60 60 60 60 60

Area of Stack Square Feet 89.150 89.150 89.150 89.150 89.150 89.150

Average Orifice Pressure (H) Inches Water 1.5 1.5 1.5 1.5 1.5 1.5

Average Stack Temperature Degrees F 325 295 295 325 295 295

Average Meter Temperature Degrees F 76 82 85 77 81 83

Final Volume of H2SO4 Solution Milliliters 70.00 56.00 64.00 120.00 128.00 124.00

Normality of Titrant (BaCl2) Equlivents/Liter 0.0991 0.0991 0.0991 0.0991 0.0991 0.0991

Volume of Aloquit (H2SO4) Milliliters 25.00 25.00 25.00 25.00 25.00 25.00

Volume of Titrant for H2SO4 Blank Milliliters 0.00 0.00 0.00 0.00 0.00 0.00

Volume of Titrant For H2SO4 Aloquit Milliliters 0.07 0.25 0.18 3.20 3.95 3.40

RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Volume of Gas Sampled Standard Dry 39.549 39.237 39.138 35.053 35.706 35.458

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.04 30.04 30.04 30.04 30.04 30.04

Water vapor in Stack Gas Percent 8.6 8.6 9.0 10.8 8.4 8.5

Stack Gas Flow Rate Actual Cubic 290,707 290,707 290,707 290,707 290,707 290,707

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 206,814 206,814 206,814 206,814 206,814 206,814

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,146 191,146 191,146 191,146 191,146 191,146

 Feet Per Minute

Heat Input (O2 F Factor) Million Btu per Hour 780 780 780 780 780 780

Post Test Meter Correction Factor dimensionless 0.98 0.98 0.98 1.01 0.98 0.99

Percent Difference Allowed 5% 0.1 0.3 0.3 2.4 0.2 0.7

Concentration of Sulfuric Acid Grains per Standard 0.000 0.001 0.001 0.033 0.042 0.036

 Dry Cubic Foot

Sulfuric Acid Emission Rate Pounds per Hour 0.609 1.753 1.447 53.837 69.589 58.433

Sulfuric Acid Emission Rate PPM 0.209 0.601 0.496 18.441 23.838 20.016

Calculations

TABLE I. SULFURIC ACID MIST EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 5
ATTACHMENT 25 - Crist Report 25 Test Results

2006 SO2 Emissions Test (Based on RATA Test)

Run Time Time RM-6C (SO2)

Number Started Stopped lbs/mmBtu

1 2/24/2006 18:19 2/24/2006 19:19 0.975

2 2/24/2006 19:42 2/24/2006 20:42 0.982

3 2/24/2006 21:05 2/24/2006 22:05 0.981

4 2/24/2006 22:28 2/24/2006 22:49 0.969

5 2/24/2006 23:12 2/24/2006 23:33 0.976

6 2/25/2006 12:06 2/25/2006 12:27 1.036

7 2/25/2006 12:50 2/25/2006 13:11 1.037

8 2/25/2006 13:34 2/25/2006 13:55 1.043

9 2/25/2006 14:24 2/25/2006 14:45 1.047

1.005

Crist Unit 6 High Load ~ 318 MW
ATTACHMENT 26 - Crist Report 26 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 3/6/2006 3/6/2006 3/6/2006

Sampling Time -Start Military 0713 0828 0936

Sampling Time -Stop Military 0813 0928 1036

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.30 0.30 0.30

Barometric Pressure Inches Mercury 30.20 30.20 30.20

Standard Orifice Pressure H@ Inches Water 1.847 1.847 1.847

Meter Correction Factor dimensionless 1.008 1.008 1.008

Oxygen Concentration Mole Percent O2 8.0 8.0 8.0

Carbon Dioxide Concentration Mole Percent CO2 11.0 11.0 11.0

Volume of Gas Metered Actual Cubic Feet 40.775 40.457 41.095

Volume of Water Collected Milliliters 60.00 66.00 74.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.200 0.200 0.200

Weight of Solids Collected Milligrams 20.2 10.3 11.7

Area of Stack Square Feet 270.000 270.000 270.000

Avg. Sqr. Root Velocity Pressure Inches Water 1.2466 1.2419 1.2625

Average Orifice Pressure (H) Inches Water 1.7 1.7 1.7

Average Stack Temperature Degrees F 322 327 331

Average Meter Temperature Degrees F 66 70 77

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 41.810 41.164 41.286 41.420

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 29.32 29.23 29.14 29.23

Water vapor in Stack Gas Percent 6.3 7.0 7.8 7.0

Average Stack Gas Velocity Feet per second 84.1 84.1 85.9 84.7

Stack Gas Flow Rate Actual Cubic 1,362,004 1,362,927 1,391,410 1,372,114

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 928,987 923,980 938,357 930,441

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 870,206 859,141 865,350 864,899

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 65,178 64,350 64,815 64,781

Per Minute

Particulate Concentration Grains per Standard 0.0074 0.0039 0.0044 0.0052

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0048 0.0024 0.0027 0.0033

 Cubic Foot

Particulate Emission Rate Pounds per Hour 55.5 28.4 32.4 38.7

Particulate Emission Rate Pounds per Million 0.017 0.009 0.010 0.012

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 3,295 3,253 3,277 3,275

Isokinetic Rate Percent 99.1 98.8 98.4 98.8

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

SOOT BLOWING OPERATIONS
ATTACHMENT 27 - Crist Report 27 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 3/6/2006 3/6/2006 3/6/2006

Sampling Time -Start Military 1205 1315 1424

Sampling Time -Stop Military 1305 1415 1524

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.30 0.30 0.30

Barometric Pressure Inches Mercury 30.20 30.20 30.20

Standard Orifice Pressure H@ Inches Water 1.847 1.847 1.847

Meter Correction Factor dimensionless 1.008 1.008 1.008

Oxygen Concentration Mole Percent O2 7.5 7.5 8.0

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.5 11.0

Volume of Gas Metered Actual Cubic Feet 41.555 41.947 41.445

Volume of Water Collected Milliliters 70.00 74.00 71.00

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.200 0.200 0.200

Weight of Solids Collected Milligrams 13.2 15.2 5.4

Area of Stack Square Feet 270.000 270.000 270.000

Avg. Sqr. Root Velocity Pressure Inches Water 1.2600 1.2744 1.2500

Average Orifice Pressure (H) Inches Water 1.7 1.8 1.7

Average Stack Temperature Degrees F 332 337 339

Average Meter Temperature Degrees F 83 89 90

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 41.296 41.259 40.682 41.079

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 29.24 29.19 29.16 29.20

Water vapor in Stack Gas Percent 7.4 7.8 7.6 7.6

Average Stack Gas Velocity Feet per second 85.6 87.0 85.5 86.0

Stack Gas Flow Rate Actual Cubic 1,387,121 1,408,933 1,384,416 1,393,490

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 934,243 942,462 923,667 933,457

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 865,210 869,092 853,550 862,617

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 64,804 65,095 63,931 64,610

Per Minute

Particulate Concentration Grains per Standard 0.0049 0.0057 0.0020 0.0042

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0031 0.0035 0.0013 0.0026

 Cubic Foot

Particulate Emission Rate Pounds per Hour 36.5 42.3 15.0 31.2

Particulate Emission Rate Pounds per Million 0.011 0.012 0.005 0.009

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 3,403 3,419 3,232 3,351

Isokinetic Rate Percent 98.4 97.9 98.3 98.2

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

STEADY STATE OPERATIONS
ATTACHMENT 28 - Crist Report 28 Test Results

Title of Run RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Date Month/Day/Year 9/19/2006 9/19/2006 9/19/2006 9/19/2006 9/19/2006 9/19/2006

Sampling Time -Start Military 0917 1102 1245 0917 1102 1245

Sampling Time -Stop Military 1017 1202 1345 1017 1202 1345

Number of Ports dimensionless 1 1 1 1 1 1

Number of Points per Port dimensionless 12 12 12 12 12 12

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water 3.00 3.00 3.00 3.00 3.00 3.00

Barometric Pressure Inches Mercury 29.90 29.90 29.90 29.90 29.90 29.90

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858 2.258 2.258 2.258

Meter Correction Factor dimensionless 0.978 0.978 0.978 0.982 0.982 0.982

Oxygen Concentration Mole Percent O2 7.0 7.0 7.0 7.0 7.0 7.0

Carbon Dioxide Concentration Mole Percent CO2 11 11 11 11 11 11

Volume of Gas Metered Actual Cubic Feet 40.705 41.015 41.540 36.553 37.290 36.781

Volume of Water Collected Milliliters 98.00 89.00 81.00 90 70 70

Sampling Time Minutes 60 60 60 60 60 60

Area of Stack Square Feet 270.000 270.000 270.000 270.000 270.000 270.000

Average Orifice Pressure (H) Inches Water 1.5 1.5 1.5 1.5 1.5 1.5

Average Stack Temperature Degrees F 333 337 337 336 337 337

Average Meter Temperature Degrees F 86 89 90 91 93 94

Final Volume of H2SO4 Solution Milliliters 90.00 50.00 80.00 164.00 193.00 189.00

Normality of Titrant (BaCl2) Equlivents/Liter 0.0991 0.0991 0.0991 0.0991 0.0991 0.0991

Volume of Aloquit (H2SO4) Milliliters 25.00 20.00 25.00 25.00 25.00 25.00

Volume of Titrant for H2SO4 Blank Milliliters 0.00 0.00 0.00 0.00 0.00 0.00

Volume of Titrant For H2SO4 Aloquit Milliliters 0.12 0.14 0.27 0.70 0.58 0.83

RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Volume of Gas Sampled Standard Dry 38.615 38.714 39.115 34.492 35.071 34.519

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.04 30.04 30.04 30.04 30.04 30.04

Water vapor in Stack Gas Percent 10.7 9.8 8.9 10.9 8.6 8.7

Stack Gas Flow Rate Actual Cubic 1,393,490 1,393,490 1,393,490 1,393,490 1,393,490 1,393,490

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 933,457 933,457 933,457 933,457 933,457 933,457

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 862,617 862,617 862,617 862,617 862,617 862,617

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 64,610 64,610 64,610 64,610 64,610 64,610

Per Minute

Heat Input (O2 F Factor) Million Btu per Hour 3,520 3,520 3,520 3,520 3,520 3,520

Post Test Meter Correction Factor dimensionless 0.99 0.99 0.98 1.01 0.99 1.00

Percent Difference Allowed 5% 1.3 0.8 -0.3 2.4 0.9 2.1

Concentration of Sulfuric Acid Grains per Standard 0.001 0.001 0.002 0.010 0.009 0.014

 Dry Cubic Foot

Sulfuric Acid Emission Rate Pounds per Hour 5.944 4.834 12.247 73.817 70.178 100.182

Sulfuric Acid Emission Rate PPM 0.451 0.367 0.930 5.603 5.327 7.604

Calculations

TABLE I. SULFURIC ACID MIST EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 6
ATTACHMENT 29 - Crist Report 29 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 6/13/2006 6/13/2006 6/13/2006

Sampling Time -Start Military 0619 0740 0857

Sampling Time -Stop Military 0723 0844 0957

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.80 1.80 1.80

Barometric Pressure Inches Mercury 29.89 29.89 29.89

Standard Orifice Pressure DH@ Inches Water 1.745 1.745 1.745

Meter Correction Factor dimensionless 0.986 0.986 0.986

Oxygen Concentration Mole Percent O2 5.9 5.7 6.0

Carbon Dioxide Concentration Mole Percent CO2 10.5 10.5 11.0

Volume of Gas Metered Actual Cubic Feet 37.300 40.500 38.900

Volume of Water Collected Milliliters 79 88 76

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.185 0.187 0.180

Weight of Solids Collected Milligrams 48.1 10.8 18.0

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.2464 1.3400 1.3687

Average Orifice Pressure (DH) Inches Water 1.5 1.7 1.5

Average Stack Temperature Degrees F 295 300 308

Average Meter Temperature Degrees F 104 108 112

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 34.552 37.259 35.514 35.775

 Cubic Feet 

Molecular Wt. of Stack Gas (wet) LB/LB-MOLE 29.92 29.91 30.00 29.94

Water vapor in Stack Gas Percent 9.7 10.0 9.2 9.6

Average Stack Gas Velocity Feet per second 83.7 90.3 92.4 88.8

Stack Gas Flow Rate Actual Cubic 1,839,097 1,985,112 2,031,428 1,951,879

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,290,193 1,383,402 1,401,354 1,358,316

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,164,833 1,244,993 1,273,115 1,227,647

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 87,246 93,250 95,356 91,951

Per Minute

Particulate Concentration Grains per Standard 0.0214 0.0045 0.0078 0.0112

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0136 0.0028 0.0049 0.0071

 Cubic Foot

Particulate Emission Rate Pounds per Hour 214.0 47.6 85.2 115.6

Particulate Emission Rate Pounds per Million 0.042 0.009 0.015 0.022

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 5,129 5,555 5,568 5,417

Isokinetic Rate Percent 97.0 95.8 96.3 96.4

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

SOOT BLOWING OPERATIONS
ATTACHMENT 30 - Crist Report 30 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 6/13/2006 6/13/2006 6/13/2006

Sampling Time -Start Military 1048 1204 1312

Sampling Time -Stop Military 1151 1307 1412

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.80 1.80 1.80

Barometric Pressure Inches Mercury 29.97 29.97 29.97

Standard Orifice Pressure DH@ Inches Water 1.745 1.745 1.745

Meter Correction Factor dimensionless 0.986 0.986 0.986

Oxygen Concentration Mole Percent O2 5.5 5.9 5.5

Carbon Dioxide Concentration Mole Percent CO2 11.0 11.0 11.5

Volume of Gas Metered Actual Cubic Feet 36.100 40.100 36.700

Volume of Water Collected Milliliters 82 88 78

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.177 0.185 0.181

Weight of Solids Collected Milligrams 35.4 24.5 9.2

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3595 1.3719 1.3314

Average Orifice Pressure (DH) Inches Water 1.4 1.6 1.4

Average Stack Temperature Degrees F 320 320 323

Average Meter Temperature Degrees F 112 110 117

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 33.033 36.815 33.286 34.378

 Cubic Feet 

Molecular Wt. of Stack Gas (wet) LB/LB-MOLE 28.73 28.78 28.86 28.79

Water vapor in Stack Gas Percent 10.5 10.1 9.9 10.2

Average Stack Gas Velocity Feet per second 92.7 93.5 90.8 92.3

Stack Gas Flow Rate Actual Cubic 2,037,042 2,053,752 1,994,729 2,028,508

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,387,222 1,398,363 1,352,336 1,379,307

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,242,091 1,256,942 1,217,989 1,239,007

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 93,033 94,145 91,227 92,802

Per Minute

Particulate Concentration Grains per Standard 0.0165 0.0102 0.0043 0.0103

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0101 0.0063 0.0026 0.0063

 Cubic Foot

Particulate Emission Rate Pounds per Hour 175.7 110.4 44.4 110.2

Particulate Emission Rate Pounds per Million 0.031 0.020 0.008 0.020

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 5,615 5,534 5,506 5,552

Isokinetic Rate Percent 95.0 95.8 93.3 94.7

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

STEADY STATE OPERATIONS
ATTACHMENT 31 - Crist Report 31 Test Results

Run Time Time Unit RM-6C

Number Started Stopped Load lbs/mmBtu

1 9/12/2006 6:12 9/12/2006 6:33 470 0.813

2 9/12/2006 7:12 9/12/2006 7:33 471 0.793

3 9/12/2006 9:07 9/12/2006 9:28 476 0.807

4 9/12 10:12 9/12 10:33 477 0.824

5 9/12 11:00 9/12 11:21 477 0.840

6 9/12 11:54 9/12 12:15 477 0.825

7 9/12 12:40 9/12 13:01 479 0.868

8 9/12 13:29 9/12 13:50 476 0.937

9 9/12 15:15 9/12 15:36 479 1.052

10 9/12 14:25 9/12 14:46 481 1.165

11 9/12 16:15 9/12 16:36 482 1.120

12 9/12 17:01 9/12 17:22 482 1.149

0.933

Crist Unit 7
ATTACHMENT 32 - Crist Report 32 Test Results

UNIT 7 UNIT 7 UNIT 7 UNIT 7 UNIT 7 UNIT 7

Title of Run RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Date Month/Day/Year 9/18/2006 9/18/2006 9/18/2006 9/18/2006 9/18/2006 9/18/2006

Sampling Time -Start Military 1050 1235 1440 1050 1235 1440

Sampling Time -Stop Military 1150 1335 1540 1150 1335 1540

Number of Ports dimensionless 1 1 1 1 1 1

Number of Points per Port dimensionless 12 12 12 12 12 12

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water 5.00 5.00 5.00 5.00 5.00 5.00

Barometric Pressure Inches Mercury 29.90 29.90 29.90 29.90 29.90 29.90

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858 2.258 2.258 2.258

Meter Correction Factor dimensionless 0.978 0.978 0.978 0.982 0.982 0.982

Oxygen Concentration Mole Percent O2 7.0 7.0 7.0 7.0 7.0 7.0

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.5 11.5 11.5 11.5 11.5

Volume of Gas Metered Actual Cubic Feet 40 41 40 37 37 36

Volume of Water Collected Milliliters 75 89 75 69 74 61

Sampling Time Minutes 60 60 60 60 60 60

Area of Stack Square Feet 366.263 366.263 366.263 366.263 366.263 366.263

Average Orifice Pressure (H) Inches Water 1.5 1.5 1.5 1.5 1.5 1.5

Average Stack Temperature Degrees F 330 329 335 331 331 333

Average Meter Temperature Degrees F 96 95 99 97 98 97

Final Volume of H2SO4 Solution Milliliters 50.00 66.00 65.00 135.00 143.00 108.00

Normality of Titrant (BaCl2) Equlivents/Liter 0.0991 0.0991 0.0991 0.0991 0.0991 0.0991

Volume of Aloquit (H2SO4) Milliliters 10.00 15.00 25.00 25.00 25.00 25.00

Volume of Titrant for H2SO4 Blank Milliliters 0.00 0.00 0.00 0.00 0.00 0.00

Volume of Titrant For H2SO4 Aloquit Milliliters 0.20 0.25 0.85 2.10 1.90 0.38

RUN 1 M8A RUN 2 M8A RUN 3 M8A RUN 1 M8 RUN 2 M8 RUN 3 M8

Volume of Gas Sampled Standard Dry 37.717 38.349 37.412 34.073 34.736 33.669

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.12 30.12 30.12 30.12 30.12 30.12

Water vapor in Stack Gas Percent 8.6 9.8 8.6 8.7 9.1 7.9

Stack Gas Flow Rate Actual Cubic 2,028,508 2,028,508 2,028,508 2,028,508 2,028,508 2,028,508

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,379,307 1,379,307 1,379,307 1,379,307 1,379,307 1,379,307

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,239,007 1,239,007 1,239,007 1,239,007 1,239,007 1,239,007

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 92,802 92,802 92,802 92,802 92,802 92,802

Per Minute

Heat Input (O2 F Factor) Million Btu per Hour 5,055 5,055 5,055 5,055 5,055 5,055

Post Test Meter Correction Factor dimensionless 1.00 0.99 1.01 1.01 0.99 1.02

Percent Difference Allowed 5% 2.7 1.1 3.2 3.0 1.0 4.2

Concentration of Sulfuric Acid Grains per Standard 0.002 0.002 0.004 0.025 0.023 0.004

 Dry Cubic Foot

Sulfuric Acid Emission Rate Pounds per Hour 21.115 22.843 47.044 265.050 249.167 38.318

Sulfuric Acid Emission Rate PPM 1.116 1.207 2.486 14.007 13.167 2.025

Calculations

TABLE I. SULFURIC ACID MIST EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST

UNIT 7
ATTACHMENT 33 - Crist Report 33 Test Results

2007 SO2 Emissions Test (Based on RATA Test)

Crist Unit 4

Run Time Time Unit RM-6C (SO2)

Number Started Stopped Load lbs/mmBtu

1 5/1/07 11:36 5/1/07 11:57 80 1.422

2 5/1/07 11:01 5/1/07 11:22 80 1.442

3 5/1/07 10:24 5/1/07 10:45 80 1.441

4 5/1/07 9:47 5/1/07 10:08 80 1.458

5 5/1/07 9:09 5/1/07 9:30 80 1.465

6 5/1/07 8:30 5/1/07 8:51 80 1.472

7 5/1/07 7:53 5/1/07 8:14 80 1.482

8 5/1/07 7:15 5/1/07 7:36 80 1.482

9 5/1/07 6:38 5/1/07 6:59 80 1.512

10 5/1/07 6:00 5/1/07 6:21 80 1.516

1.469
ATTACHMENT 34 - Crist Report 34 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/1/2007 5/1/2007 5/1/2007

Sampling Time -Start Military 1212 1330 1449

Sampling Time -Stop Military 1318 1437 1555

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.90 -0.90 -0.90

Barometric Pressure Inches Mercury 30.10 30.10 30.10

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858

Meter Correction Factor dimensionless 0.978 0.978 0.978

Oxygen Concentration Mole Percent O2 6.5 6.5 6.5

Carbon Dioxide Concentration Mole Percent CO2 12.5 12.5 12

Volume of Gas Metered Actual Cubic Feet 36.648 36.255 36.754

Volume of Water Collected Milliliters 127 129 125

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.216 0.218 0.218

Weight of Solids Collected Milligrams 14.9 16.3 14.3

Area of Stack Square Feet 89.169 89.169 89.169

Avg. Sqr. Root Velocity Pressure Inches Water 0.8679 0.8639 0.8656

Average Orifice Pressure (H) Inches Water 1.1 1.1 1.1

Average Stack Temperature Degrees F 303 304 303

Average Meter Temperature Degrees F 84 85 85

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 35.087 34.656 35.133 34.959

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.26 30.26 30.18 30.23

Water vapor in Stack Gas Percent 14.6 14.9 14.3 14.6

Average Stack Gas Velocity Feet per second 58.9 58.7 58.8 58.8

Stack Gas Flow Rate Actual Cubic 314,938 313,879 314,355 314,391

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 218,654 217,696 218,214 218,188

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 186,824 185,240 186,912 186,325

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 13,993 13,875 14,000 13,956

Per Minute

Particulate Concentration Grains per Standard 0.007 0.007 0.006 0.007

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.004 0.004 0.004 0.004

 Cubic Foot

Particulate Emission Rate Pounds per Hour 10.5 11.5 10.0 10.7

Particulate Emission Rate Pounds per Million 0.013 0.015 0.013 0.014

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 790 783 790 788

Isokinetic Rate Percent 102.8 100.5 101.0 101.5

Post Test Meter Correction Factor dimensionless 0.99 1.00 0.99 0.99

Percent Difference Allowed 5% 1.3 2.1 0.9 1.4

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 4 

SOOT BLOWING OPERATIONS
ATTACHMENT 35 - Crist Report 35 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/1/2007 5/1/2007 5/1/2007

Sampling Time -Start Military 0640 0802 0924

Sampling Time -Stop Military 0747 0909 1033

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.90 -0.90 -0.90

Barometric Pressure Inches Mercury 30.10 30.10 30.10

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858

Meter Correction Factor dimensionless 0.978 0.978 0.978

Oxygen Concentration Mole Percent O2 7.5 7 7

Carbon Dioxide Concentration Mole Percent CO2 12 12.5 12.5

Volume of Gas Metered Actual Cubic Feet 38.795 37.847 38.013

Volume of Water Collected Milliliters 108 129 135

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.220 0.218 0.220

Weight of Solids Collected Milligrams 40.3 32.3 27.2

Area of Stack Square Feet 89.169 89.169 89.169

Avg. Sqr. Root Velocity Pressure Inches Water 0.8580 0.8627 0.8657

Average Orifice Pressure (H) Inches Water 1.2 1.2 1.2

Average Stack Temperature Degrees F 288 295 299

Average Meter Temperature Degrees F 71 79 83

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 38.068 36.611 36.480 37.053

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.22 30.28 30.28 30.26

Water vapor in Stack Gas Percent 11.8 14.2 14.8 13.6

Average Stack Gas Velocity Feet per second 57.3 58.1 58.6 58.0

Stack Gas Flow Rate Actual Cubic 306,670 311,003 313,439 310,370

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 217,157 218,355 218,715 218,075

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,574 187,291 186,269 188,378

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,349 14,028 13,952 14,110

Per Minute

Particulate Concentration Grains per Standard 0.016 0.014 0.011 0.014

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.010 0.008 0.007 0.008

 Cubic Foot

Particulate Emission Rate Pounds per Hour 26.8 21.8 18.3 22.3

Particulate Emission Rate Pounds per Million 0.036 0.029 0.024 0.029

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 754 764 760 759

Isokinetic Rate Percent 104.9 105.1 103.3 104.4

Post Test Meter Correction Factor dimensionless 0.99 1.01 1.00 1.00

Percent Difference Allowed 5% 1.0 3.4 1.9 2.1

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 4

STEADY STATE OPERATIONS
ATTACHMENT 36 - Crist Report 36 Test Results

2007 SO2 Emissions Test (Based on RATA Test)

Crist Unit 5

Run Time Time Unit RM-6C (SO2)

Number Started Stopped Load lbs/mmBtu

1 1/23/07 7:02 1/23/07 7:23 75 0.876

2 1/23/07 7:44 1/23/07 8:05 75 0.869

3 1/23/07 8:25 1/23/07 8:46 75 0.865

4 1/23/07 9:04 1/23/07 9:25 76 0.880

5 1/23/07 9:44 1/23/07 10:05 72 0.903

6 1/23/07 10:25 1/23/07 10:46 76 0.911

7 1/23/07 11:05 1/23/07 11:26 76 0.916

8 1/23/07 11:46 1/23/07 12:07 75 0.930

9 1/23/07 12:28 1/23/07 12:49 76 0.940

10 1/23/07 13:17 1/23/07 13:38 76 0.941

0.903
ATTACHMENT 37 - Crist Report 37 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/23/2007 1/23/2007 1/23/2007

Sampling Time -Start Military 0724 0906 1030

Sampling Time -Stop Military 0835 1013 1137

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,720 9,720 9,720

Stack Static Pressure Inches Water -0.95 -0.95 -0.95

Barometric Pressure Inches Mercury 30.25 30.25 30.25

Standard Orifice Pressure H@ Inches Water 1.939 1.939 1.939

Meter Correction Factor dimensionless 0.981 0.981 0.981

Oxygen Concentration Mole Percent O2 7.5 8.0 8.0

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.5 11.0

Volume of Gas Metered Actual Cubic Feet 39.050 38.393 37.930

Volume of Water Collected Milliliters 57 65 70

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.230 0.230 0.230

Weight of Solids Collected Milligrams 25.4 24.7 24.9

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8073 0.7928 0.7788

Average Orifice Pressure (H) Inches Water 1.3 1.3 1.2

Average Stack Temperature Degrees F 275 275 274

Average Meter Temperature Degrees F 51 52 52

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 40.169 39.400 38.958 39.509

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.14 30.16 30.08 30.13

Water vapor in Stack Gas Percent 6.3 7.2 7.8 7.1

Average Stack Gas Velocity Feet per second 52.8 51.9 51.1 51.9

Stack Gas Flow Rate Actual Cubic 282,293 277,561 273,204 277,686

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 204,491 201,226 198,270 201,329

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 191,688 186,726 182,809 187,074

 Feet Per Minute

Particulate Concentration Grains per Standard 0.010 0.010 0.010 0.010

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.007 0.006 0.007 0.007

 Cubic Foot

Particulate Emission Rate Pounds per Hour 16.0 15.5 15.4 15.6

Particulate Emission Rate Pounds per Million 0.021 0.022 0.022 0.022

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 759 711 697 722

Isokinetic Rate Percent 101.2 101.8 102.9 102.0

Post Test Meter Correction Factor dimensionless 0.97 0.97 0.96 0.97

Percent Difference Allowed 5% -1.0 -1.1 -1.6 -1.2

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 5

SOOT BLOWING OPERATIONS
ATTACHMENT 38 - Crist Report 38 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 1/23/2007 1/23/2007 1/23/2007

Sampling Time -Start Military 1325 1458 1615

Sampling Time -Stop Military 1432 1605 1725

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,720 9,720 9,720

Stack Static Pressure Inches Water -0.95 -0.95 -0.95

Barometric Pressure Inches Mercury 30.25 30.25 30.25

Standard Orifice Pressure H@ Inches Water 1.939 1.939 1.939

Meter Correction Factor dimensionless 0.981 0.981 0.981

Oxygen Concentration Mole Percent O2 7.0 7.5 8.0

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.5 11.0

Volume of Gas Metered Actual Cubic Feet 36.385 36.285 36.225

Volume of Water Collected Milliliters 61 67 66

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.230 0.230 0.230

Weight of Solids Collected Milligrams 21.6 24.8 20.4

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.7440 0.7416 0.7370

Average Orifice Pressure (H) Inches Water 1.1 1.1 1.1

Average Stack Temperature Degrees F 277 281 281

Average Meter Temperature Degrees F 55 56 56

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 37.130 36.905 36.907 36.981

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.12 30.14 30.08 30.11

Water vapor in Stack Gas Percent 7.2 7.9 7.8 7.6

Average Stack Gas Velocity Feet per second 48.8 48.8 48.6 48.7

Stack Gas Flow Rate Actual Cubic 261,030 261,142 259,711 260,628

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 188,671 187,772 186,751 187,731

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 175,128 172,989 172,252 173,456

 Feet Per Minute

Particulate Concentration Grains per Standard 0.009 0.010 0.009 0.009

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.006 0.007 0.006 0.006

 Cubic Foot

Particulate Emission Rate Pounds per Million 0.019 0.022 0.019 0.020

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 719 685 656 687

Isokinetic Rate Percent 102.3 103.0 103.4 102.9

Post Test Meter Correction Factor dimensionless 0.97 0.97 0.96 0.97

Percent Difference Allowed 5% -1.0 -1.1 -1.9 -1.3

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 5

STEADY STATE OPERATIONS
ATTACHMENT 39 - Crist Report 39 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 11/12/2007 11/12/2007 11/12/2007

Sampling Time -Start Military 1110 1225 1408

Sampling Time -Stop Military 1126 1333 1520

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.35 -0.35 -0.35

Barometric Pressure Inches Mercury 30.25 30.25 30.25

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858

Meter Correction Factor dimensionless 0.978 0.978 0.978

Oxygen Concentration Mole Percent O2 8.0 7.5 9.0

Carbon Dioxide Concentration Mole Percent CO2 11.0 12.0 11.5

Volume of Gas Metered Actual Cubic Feet 46.181 45.636 48.488

Volume of Water Collected Milliliters 84 88 96

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.245 0.248 0.250

Weight of Solids Collected Milligrams 20.7 11.8 30.4

Area of Stack Square Feet 89.15 89.15 89.15

Avg. Sqr. Root Velocity Pressure Inches Water 0.8103 0.8352 0.8523

Average Orifice Pressure (H) Inches Water 1.6 1.9 2.0

Average Stack Temperature Degrees F 290 295 299

Average Meter Temperature Degrees F 67 71 72

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 45.963 45.095 47.862 46.307

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.08 30.22 30.20 30.17

Water vapor in Stack Gas Percent 7.9 8.4 8.6 8.3

Average Stack Gas Velocity Feet per second 53.7 55.5 56.8 55.3

Stack Gas Flow Rate Actual Cubic 287,248 296,718 303,786 295,917

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 204,225 209,551 213,473 209,083

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 188,048 191,922 195,057 191,676

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,085 14,375 14,610 14,357

Per Minute

Particulate Concentration Grains per Standard 0.007 0.004 0.010 0.007

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.005 0.003 0.006 0.004

 Cubic Foot

Particulate Emission Rate Pounds per Hour 11.2 6.6 16.4 11.4

Particulate Emission Rate Pounds per Million 0.016 0.009 0.024 0.016

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 712 755 681 716

Isokinetic Rate Percent 104.0 97.6 100.2 100.6

Post Test Meter Correction Check (Yqa) dimensionless 0.95 1.03 1.00 0.99

Percent Difference Allowed 5% Average -3.2 4.8 1.9 1.2

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST -UNIT 5

PENSACOLA, FLORIDA
ATTACHMENT 40 - Crist Report 40 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 11/13/2007 11/13/2007 11/13/2007

Sampling Time -Start Military 0827 1008 1210

Sampling Time -Stop Military 0936 1126 1319

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.80 -0.80 -0.80

Barometric Pressure Inches Mercury 30.20 30.20 30.20

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.858

Meter Correction Factor dimensionless 0.978 0.978 0.978

Oxygen Concentration Mole Percent O2 6.5 6.0 5.5

Carbon Dioxide Concentration Mole Percent CO2 14.0 13.0 13.0

Volume of Gas Metered Actual Cubic Feet 44.633 47.480 44.694

Volume of Water Collected Milliliters 98 98 86

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.248 0.252 0.245

Weight of Solids Collected Milligrams 12.4 51.1 9.7

Area of Stack Square Feet 89.15 89.15 89.15

Avg. Sqr. Root Velocity Pressure Inches Water 0.8135 0.8280 0.8306

Average Orifice Pressure (H) Inches Water 1.7 1.9 1.7

Average Stack Temperature Degrees F 289 294 296

Average Meter Temperature Degrees F 64 72 74

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 44.576 46.751 43.810 45.046

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.50 30.32 30.30 30.37

Water vapor in Stack Gas Percent 9.4 9.0 8.5 8.9

Average Stack Gas Velocity Feet per second 53.8 55.0 55.2 54.7

Stack Gas Flow Rate Actual Cubic 287,538 294,276 295,362 292,392

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 204,217 207,512 207,727 206,486

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 185,066 188,876 190,157 188,033

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 13,861 14,147 14,243 14,084

Per Minute

Particulate Concentration Grains per Standard 0.004 0.017 0.003 0.008

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.003 0.011 0.002 0.005

 Cubic Foot

Particulate Emission Rate Pounds per Hour 6.8 27.3 5.6 13.2

Particulate Emission Rate Pounds per Million 0.009 0.033 0.006 0.016

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 782 826 860 823

Isokinetic Rate Percent 100.0 99.5 98.0 99.2

Post Test Meter Correction Check (Yqa) dimensionless 0.99 0.99 1.00 0.99

Percent Difference Allowed 5% Average 1.3 1.1 2.3 1.6

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST -UNIT 5

PENSACOLA, FLORIDA
ATTACHMENT 41 - Crist Report 41 Test Results

2007 SO2 Emissions Test (Based on RATA Test)

Crist Unit 6

Run Time Time Unit RM-6C (SO2)

Number Started Stopped Load lbs/mmBtu

1 2/16/07 6:50 2/16/07 7:11 318 1.181

2 2/16/07 7:31 2/16/07 7:52 318 1.193

3 2/16/07 8:10 2/16/07 8:31 318 1.179

4 2/16/07 6:50 2/16/07 7:11 319 1.140

5 2/16/07 8:49 2/16/07 9:10 318 1.094

6 2/16/07 10:19 2/16/07 10:40 318 1.077

7 2/16/07 10:58 2/16/07 11:19 317 1.068

8 2/16/07 11:37 2/16/07 11:58 318 1.080

9 2/16/07 12:17 2/16/07 12:38 317 1.118

1.126
ATTACHMENT 42 - Crist Report 42 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 2/20/2007 2/20/2007 2/20/2007

Sampling Time -Start Military 0720 0844 1009

Sampling Time -Stop Military 0820 0944 1109

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.30 0.30 0.30

Barometric Pressure Inches Mercury 30.15 30.15 30.15

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 8.5 8 8

Carbon Dioxide Concentration Mole Percent CO2 11.5 12 11.5

Volume of Gas Metered Actual Cubic Feet 50.348 51.995 50.763

Volume of Water Collected Milliliters 116 91 104

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.215 0.215 0.215

Weight of Solids Collected Milligrams 7.0 19.3 6.6

Area of Stack Square Feet 270.000 270.000 270.000

Avg. Sqr. Root Velocity Pressure Inches Water 1.2336 1.2556 1.2326

Average Orifice Pressure (H) Inches Water 2.8 3.0 2.9

Average Stack Temperature Degrees F 316 308 322

Average Meter Temperature Degrees F 62 64 70

Calculations

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 48.532 49.981 48.198 48.904

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.18 30.24 30.16 30.19

Water vapor in Stack Gas Percent 10.1 7.9 9.2 9.1

Average Stack Gas Velocity Feet per second 83.5 84.1 83.6 83.7

Stack Gas Flow Rate Actual Cubic 1,351,963 1,362,122 1,354,347 1,356,144

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 928,015 943,754 922,039 931,269

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 834,167 869,259 837,026 846,817

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 62,479 65,108 62,693 63,427

Per Minute

Particulate Concentration Grains per Standard 0.002 0.006 0.002 0.003

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.004 0.001 0.002

 Cubic Foot

Particulate Emission Rate Pounds per Hour 15.9 44.3 15.1 25.1

Particulate Emission Rate Pounds per Million 0.005 0.013 0.005 0.008

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 3,036 3,292 3,170 3,166

Isokinetic Rate Percent 103.8 102.6 102.8 103.1

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

SOOT BLOWING OPERATIONS
ATTACHMENT 43 - Crist Report 43 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 2/20/2007 2/20/2007 2/20/2007

Sampling Time -Start Military 1308 1422 1536

Sampling Time -Stop Military 1408 1522 1636

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.30 0.30 0.30

Barometric Pressure Inches Mercury 30.15 30.15 30.15

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 8 7 8

Carbon Dioxide Concentration Mole Percent CO2 11 12 11.25

Volume of Gas Metered Actual Cubic Feet 49.157 48.349 47.982

Volume of Water Collected Milliliters 74 83 85

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.215 0.210 0.208

Weight of Solids Collected Milligrams 10.6 7.7 9.3

Area of Stack Square Feet 270.000 270.000 270.000

Avg. Sqr. Root Velocity Pressure Inches Water 1.1725 1.2210 1.2288

Average Orifice Pressure (H) Inches Water 2.6 2.6 2.5

Average Stack Temperature Degrees F 314 326 330

Average Meter Temperature Degrees F 84 85 85

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 45.452 44.625 44.234 44.770

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.08 30.20 30.12 30.13

Water vapor in Stack Gas Percent 7.1 8.1 8.3 7.8

Average Stack Gas Velocity Feet per second 78.9 82.8 83.6 81.8

Stack Gas Flow Rate Actual Cubic 1,277,979 1,341,292 1,355,056 1,324,775

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 878,667 907,924 913,522 900,037

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 816,124 834,836 837,748 829,569

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 61,128 62,529 62,747 62,135

Per Minute

Particulate Concentration Grains per Standard 0.004 0.003 0.003 0.003

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.002 0.002 0.002 0.002

 Cubic Foot

Particulate Emission Rate Pounds per Hour 25.1 19.0 23.2 22.5

Particulate Emission Rate Pounds per Million 0.008 0.006 0.007 0.007

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 3,090 3,406 3,172 3,223

Isokinetic Rate Percent 99.4 100.0 100.7 100.0

Calculations

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

STEADY STATE OPERATIONS
ATTACHMENT 44 - Crist Report 44 Test Results

Title of Run Description Date Start Time End Time Test Load

Avg. Econ 

Gas Outlet 

CO 

Avg. Econ 

Gas Outlet 

O2 

Avg. Econ 

Gas Outlet 

CO2 

Avg. Econ 

Gas Outlet 

Temp 

Military Military MW ppm % dry % dry DEGF 

Test 01 Full Load 8/24/2006 8:50 9:50 489 444 3.24 15.89 699

Test 03 Full Load 8/25/2006 9:09 10:09 486 69 3.29 15.7 699

Test 06 Full Load 1/11/2007 15:35 16:35 501 8 4.06 14.86 699

Test 08 Full Load 1/12/2007 9:13 10:13 497 7 4.01 14.93 700

Air Preheater Performance Test Results Summary

Crist Unit 7
ATTACHMENT 45 - Crist Report 45 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 3/9/2007 3/9/2007 3/9/2007

Sampling Time -Start Military 0807 0928 1045

Sampling Time -Stop Military 0911 1031 1148

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.25 1.25 1.25

Barometric Pressure Inches Mercury 30.15 30.15 30.15

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 6 6 6

Carbon Dioxide Concentration Mole Percent CO2 12 12 12

Volume of Gas Metered Actual Cubic Feet 41.550 42.977 42.458

Volume of Water Collected Milliliters 59 60 73

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.185 0.190 0.190

Weight of Solids Collected Milligrams 8.9 30.2 21.2

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3404 1.3409 1.3327

Average Orifice Pressure (H) Inches Water 2.2 2.4 2.3

Average Stack Temperature Degrees F 306 316 321

Average Meter Temperature Degrees F 74 82 78

Calculations

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 39.053 39.881 39.684 39.539

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.16 30.16 30.16 30.16

Water vapor in Stack Gas Percent 6.6 6.6 8.0 7.1

Average Stack Gas Velocity Feet per second 89.4 90.0 90.0 89.8

Stack Gas Flow Rate Actual Cubic 1,964,754 1,978,299 1,977,737 1,973,597

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,368,243 1,359,802 1,351,231 1,359,759

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,277,404 1,269,875 1,243,555 1,263,611

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 95,678 95,114 93,142 94,644

Per Minute

Particulate Concentration Grains per Standard 0.004 0.012 0.008 0.008

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.002 0.007 0.005 0.005

 Cubic Foot

Particulate Emission Rate Pounds per Hour 38.4 126.9 87.7 84.4

Particulate Emission Rate Pounds per Million 0.007 0.023 0.016 0.015

Allwoable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 5,587 5,554 5,439 5,527

Isokinetic Rate Percent 100.0 97.3 98.9 98.7

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

STEADY STATE OPERATIONS
ATTACHMENT 46 - Crist Report 46 Test Results

2007 SO2 Emissions Test (Based on RATA Test)

Crist Unit 7 

Run Time Time Unit RM-6C (SO2)

Number Started Stopped Load lbs/mmBtu

1 9/25/07 6:16 9/25/07 6:37 499 1.146

2 9/25/07 6:56 9/25/07 7:17 497 1.142

3 9/25/07 7:36 9/25/07 7:57 500 1.142

4 9/25/07 8:15 9/25/07 8:36 497 1.143

5 9/25/07 8:56 9/25/07 9:17 499 1.142

6 9/25/07 9:37 9/25/07 9:58 500 1.140

7 9/25/07 10:18 9/25/07 10:39 501 1.140

8 9/25/07 10:59 9/25/07 11:20 500 1.144

9 9/25/07 11:41 9/25/07 11:55 499 1.144

10 9/25/07 12:14 9/25/07 12:35 501 1.136

11 9/25/07 12:55 9/25/07 13:16 502 1.146

12 9/25/07 13:36 9/25/07 13:57 500 1.134

1.142
ATTACHMENT 47 - Crist Report 47 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 9/25/2007 9/25/2007 9/25/2007

Sampling Time -Start Military 0720 0904 1028

Sampling Time -Stop Military 0828 1013 1136

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.30 1.30 1.30

Barometric Pressure Inches Mercury 30.08 30.08 30.08

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 5.5 5.5 5.5

Carbon Dioxide Concentration Mole Percent CO2 12.0 11.5 12.0

Volume of Gas Metered Actual Cubic Feet 42.275 44.071 41.904

Volume of Water Collected Milliliters 67 75 80

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.188 0.188 0.186

Weight of Solids Collected Milligrams 8.8 8.3 8.1

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3174 1.3574 1.3809

Average Orifice Pressure (H) Inches Water 2.0 2.2 2.2

Average Stack Temperature Degrees F 319 326 330

Average Meter Temperature Degrees F 85 87 92

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 38.879 40.417 38.048 39.115

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.14 30.06 30.14 30.11

Water vapor in Stack Gas Percent 7.5 8.0 9.0 8.2

Average Stack Gas Velocity Feet per second 88.9 92.2 94.1 91.7

Stack Gas Flow Rate Actual Cubic 1,953,398 2,026,117 2,067,754 2,015,756

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,335,039 1,373,041 1,394,392 1,367,491

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,234,873 1,262,745 1,268,817 1,255,478

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 92,492 94,580 95,034 94,035

Per Minute

Particulate Concentration Grains per Standard 0.003 0.003 0.003 0.003

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.002 0.002 0.002 0.002

 Cubic Foot

Particulate Emission Rate Pounds per Hour 36.9 34.2 35.7 35.6

Particulate Emission Rate Pounds per Million 0.007 0.006 0.006 0.006

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 5,582 5,708 5,736 5,675

Isokinetic Rate Percent 99.7 101.3 97.0 99.3

Post Test Meter Correction Check (Yqa) dimensionless 0.97 0.96 1.01 0.98

Percent Difference Allowed 5% Average 3.2 2.2 7.4 4.3

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

SOOT BLOWING OPERATIONS
ATTACHMENT 48 - Crist Report 48 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 9/26/2007 9/26/2007 9/26/2007

Sampling Time -Start Military 0722 0917 1104

Sampling Time -Stop Military 0829 1025 1211

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.35 1.35 1.35

Barometric Pressure Inches Mercury 30.04 30.04 30.04

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 4.0 4.0 4.0

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.5 11.5

Volume of Gas Metered Actual Cubic Feet 43.433 44.139 46.588

Volume of Water Collected Milliliters 73 80 88

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.186 0.188 0.188

Weight of Solids Collected Milligrams 14.5 18.9 24.8

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3930 1.3793 1.4311

Average Orifice Pressure (H) Inches Water 2.2 2.2 2.4

Average Stack Temperature Degrees F 319 329 334

Average Meter Temperature Degrees F 89 89 96

Calculations

RUN 1 RUN 2 RUN 3 Average

Volume of Gas Sampled Standard Dry 39.583 40.218 41.926 40.576

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.00 30.00 30.00 30.00

Water vapor in Stack Gas Percent 8.0 8.6 9.0 8.5

Average Stack Gas Velocity Feet per second 94.3 94.1 98.1 95.5

Stack Gas Flow Rate Actual Cubic 2,072,830 2,068,611 2,155,221 2,098,887

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,415,686 1,394,233 1,443,213 1,417,711

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,302,610 1,274,868 1,313,449 1,296,976

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 97,565 95,488 98,377 97,143

Per Minute

Particulate Concentration Grains per Standard 0.006 0.007 0.009 0.007

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.004 0.004 0.006 0.005

 Cubic Foot

Particulate Emission Rate Pounds per Hour 63.0 79.1 102.6 81.5

Particulate Emission Rate Pounds per Million 0.010 0.013 0.016 0.013

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 6,462 6,324 6,516 6,434

Isokinetic Rate Percent 98.3 99.9 101.1 99.7

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 7

STEADY STATE OPERATIONS
ATTACHMENT 49 - Crist Report 49 Test Results

2008 SO2 Emissions Test

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LB MMBTU/HR

4 82 86000 11985 883

5 82 74400 11985 811

6 82 75000 11985 817

1.125

Started Stopped lbs/mmBtu

Crist Unit 4

Time Time RM-6C (SO2)

4/29/08 11:07 4/29/08 12:07 1.107

4/29/08 7:45 4/29/08 8:45 1.142

4/29/08 9:37 4/29/08 10:37 1.126
ATTACHMENT 50 - Crist Report 50 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 4/29/2008 4/29/2008 4/29/2008

Sampling Time -Start Military 0745 0937 1107

Sampling Time -Stop Military 0854 1043 1213

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.40 0.40 0.40

Barometric Pressure Inches Mercury 30.22 30.22 30.22

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 7.0 7.5 7.5

Carbon Dioxide Concentration Mole Percent CO2 11.0 11.0 11.0

Volume of Gas Metered Actual Cubic Feet 41.354 41.803 39.632

Volume of Water Collected Milliliters 56 70 48

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.219 0.220 0.216

Weight of Solids Collected Milligrams 6.3 3.3 4.7

Area of Stack Square Feet 89.168 89.168 89.168

Avg. Sqr. Root Velocity Pressure Inches Water 0.8816 0.8694 0.8595

Average Orifice Pressure (H) Inches Water 1.5 1.5 1.4

Average Stack Temperature Degrees F 271 274 277

Average Meter Temperature Degrees F 65 69 73

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 39.631 39.727 37.341 38.900

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.04 30.06 30.06 30.05

Water vapor in Stack Gas Percent 6.2 7.7 5.7 6.5

Average Stack Gas Velocity Feet per second 57.5 56.9 56.2 56.9

Stack Gas Flow Rate Actual Cubic 307,585 304,671 300,733 304,329

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 224,575 221,632 217,710 221,306

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 210,569 204,659 205,288 206,839

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 15,772 15,329 15,376 15,492

Per Minute

Particulate Concentration Grains per Standard 0.002 0.001 0.002 0.002

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.002 0.001 0.001 0.001

 Cubic Foot

Particulate Emission Rate Pounds per Hour 4.4 2.2 3.4 3.4

Particulate Emission Rate Pounds per Million 0.005 0.003 0.004 0.004

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 859 805 807 824

Isokinetic Rate Percent 100.2 102.4 99.6 100.7

Post Test Meter Correction Check dimensionless 0.90 0.89 0.89 0.90

Percent Difference Allowed 5% Average -3.6 -4.8 -4.6 -4.3

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 4 

SOOT BLOWING OPERATIONS
ATTACHMENT 51 - Crist Report 51 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 4/29/2008 4/29/2008 4/29/2008

Sampling Time -Start Military 1340 1602 1742

Sampling Time -Stop Military 1449 1714 1848

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.40 0.40 0.40

Barometric Pressure Inches Mercury 30.22 30.22 30.22

Standard Orifice Pressure H@ Inches Water 2.418 2.418 2.418

Meter Correction Factor dimensionless 0.939 0.939 0.939

Oxygen Concentration Mole Percent O2 7.0 7.5 7.5

Carbon Dioxide Concentration Mole Percent CO2 11.0 10.5 11.0

Volume of Gas Metered Actual Cubic Feet 39.459 42.955 40.868

Volume of Water Collected Milliliters 73 66 71

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.214 0.219 0.218

Weight of Solids Collected Milligrams 4.0 4.3 4.9

Area of Stack Square Feet 89.168 89.168 89.168

Avg. Sqr. Root Velocity Pressure Inches Water 0.8687 0.9117 0.8654

Average Orifice Pressure (H) Inches Water 1.3 1.6 1.4

Average Stack Temperature Degrees F 280 282 282

Average Meter Temperature Degrees F 75 75 74

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 37.050 40.360 38.433 38.614

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.04 29.98 30.06 30.03

Water vapor in Stack Gas Percent 8.5 7.1 8.0 7.9

Average Stack Gas Velocity Feet per second 57.2 60.1 57.0 58.1

Stack Gas Flow Rate Actual Cubic 306,268 321,313 305,210 310,930

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 221,023 231,206 219,554 223,928

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 202,265 214,682 201,990 206,312

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 15,150 16,080 15,129 15,453

Per Minute

Particulate Concentration Grains per Standard 0.002 0.002 0.002 0.002

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.001 0.001 0.001

 Cubic Foot

Particulate Emission Rate Pounds per Hour 2.9 3.0 3.4 3.1

Particulate Emission Rate Pounds per Million 0.003 0.004 0.004 0.004

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 825 844 795 821

Isokinetic Rate Percent 102.2 100.1 102.3 101.5

Post Test Meter Correction Check dimensionless 0.89 0.89 0.88 0.89

Percent Difference Allowed 5% Average -4.8 -4.4 -5.6 -4.9

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 4 

STEADY STATE OPERATIONS
ATTACHMENT 52 - Crist Report 52 Test Results

Inlet Inlet Outlet Outlet

Title of Run RUN 1 RUN 2 RUN 1 RUN 2

Date Month/Day/Year 6/5/2008 6/5/2008 6/5/2008 6/5/2008

Sampling Time -Start Military 0920 1050 0915 1050

Sampling Time -Stop Military 1000 1130 1015 1150

Number of Ports dimensionless 4 4 8 8

Number of Points per Port dimensionless 5 5 3 3

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -5.00 -5.00 -7.50 -7.50

Barometric Pressure Inches Mercury 29.80 29.80 29.80 29.80

Standard Orifice Pressure H@ Inches Water 1.858 1.858 1.939 1.939

Meter Correction Factor dimensionless 0.978 0.978 0.981 0.981

Oxygen Concentration Mole Percent O2 3.0 3.0 5.5 5.5

Carbon Dioxide Concentration Mole Percent CO2 18.0 18.0 15.0 15.5

Volume of Gas Metered Actual Cubic Feet 23.400 28.900 30.110 34.050

Volume of Water Collected Milliliters 58 69 60.2 81.5

Sampling Time Minutes 40 40 60 60

Nozzle Diameter Inches 0.300 0.330 0.273 0.301

Weight of Solids Collected Milligrams 4550.7 5839.4 38.4 51.0

Area of Stack Square Feet 72.000 72.000 72.330 72.330

Avg. Sqr. Root Velocity Pressure Inches Water 0.5477 0.5477 0.6103 0.6225

Average Orifice Pressure (H) Inches Water 1.2 1.7 0.8 1.1

Average Stack Temperature Degrees F 607 609 572 576

Average Meter Temperature Degrees F 95 98 89 92

Calculations

Inlet Inlet Outlet Outlet Inlet Outlet Efficiency

RUN 1 RUN 2 RUN 1 RUN 2 AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 21.742 26.742 28.331 31.936 24.242 30.134

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 31.00 31.00 30.62 30.70 31.00 30.66

Water vapor in Stack Gas Percent 11.2 10.8 9.1 10.7 11.0 9.9

Average Stack Gas Velocity Feet per second 43.6 43.6 48.0 49.1 43.6 48.5

Stack Gas Flow Rate Actual Cubic 188,190 188,213 208,105 213,135 188,201 210,620

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 91,565 91,422 104,013 106,137 91,494 105,075

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 81,350 81,521 94,556 94,755 81,436 94,655

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 6,093 6,106 7,082 7,097 6,100 7,090

Per Minute

Particulate Concentration Grains per Standard 3.223 3.363 0.021 0.025 3.293 0.023 99.31

 Dry Cubic Foot

Particulate Concentration Grains per Actual 1.393 1.457 0.009 0.011 1.425 0.010 99.28

 Cubic Foot

Particulate Emission Rate Pounds per Hour 2,247.6 2,349.8 16.9 20.0 2,298.7 18.4 99.20

Particulate Emission Rate Pounds per Million 5.258 5.486 0.040 0.047 5.372 0.043 99.20

 Btu (O2 F Factor)

Particulate Emission Rate Pounds per Million 5.258 5.486 0.040 0.047 5.473 0.043 99.21

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 427 428 427 428 428 428

Part Conc. 50% Excess Air Grains per Standard 2.504 2.612 0.019 0.022 2.558 0.020 99.20

 Dry Cubic Foot

Excess Air Percent 17 17 36 36 17 36

Particulate Concentration Grains per Standard Dry 2.323 2.423 0.017 0.021 2.373 0.019 99.20

 Cubic Foot @ 8% O2

Particulate Concentration Grains per Standard Dry 1.963 2.048 0.015 0.017 2.005 0.016 99.20

 Cubic Foot @ 10% O2

Isokinetic Rate Percent 98.0 99.4 88.8 82.2 98.7 85.5

Post Test Meter Correction Check dimensionless 1.01 0.98 0.93 0.97 1.00 0.95

Percent Difference Allowed 5% Average 3.2 0.7 -5.1 -1.3 1.9 -3.2

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 4

SIDE A
ATTACHMENT 53 - Crist Report 53 Test Results

Inlet Inlet Inlet Outlet Outlet Outlet

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3

Date Month/Day/Year 6/5/2008 6/5/2008 6/5/2008 6/5/2008 6/5/2008 6/5/2008

Sampling Time -Start Military 0920 1050 1220 0915 1050 1220

Sampling Time -Stop Military 1000 1130 1300 1015 1150 1320

Number of Ports dimensionless 4 4 4 8 8 8

Number of Points per Port dimensionless 5 5 5 3 3 3

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -5.00 -5.00 -5.00 -7.50 -7.50 -7.50

Barometric Pressure Inches Mercury 29.80 29.80 29.80 29.80 29.80 29.80

Standard Orifice Pressure H@ Inches Water 2.258 2.258 2.258 2.211 2.211 2.211

Meter Correction Factor dimensionless 0.982 0.982 0.982 0.927 0.927 0.927

Oxygen Concentration Mole Percent O2 4.5 4.5 4.5 6.5 6.5 6.0

Carbon Dioxide Concentration Mole Percent CO2 16.0 16.0 16.0 15.0 14.5 15.0

Volume of Gas Metered Actual Cubic Feet 22.175 22.400 22.445 32.527 40.307 41.229

Volume of Water Collected Milliliters 64.3 60.8 57.8 57.5 93.1 82.2

Sampling Time Minutes 40 40 40 60 60 60

Nozzle Diameter Inches 0.275 0.275 0.275 0.273 0.306 0.306

Weight of Solids Collected Milligrams 3767.0 4239.8 4418.3 34.5 46.2 26.5

Area of Stack Square Feet 72.000 72.000 72.000 72.330 72.330 72.330

Avg. Sqr. Root Velocity Pressure Inches Water 0.6058 0.6139 0.6039 0.6382 0.6601 0.6231

Average Orifice Pressure (H) Inches Water 1.3 1.3 1.3 1.1 1.6 1.7

Average Stack Temperature Degrees F 652 656 654 580 573 568

Average Meter Temperature Degrees F 114 120 116 86 88 88

Calculations

Inlet Inlet Inlet Outlet Outlet Outlet Inlet Outlet Efficiency

RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 AVERAGE AVERAGE

Volume of Gas Sampled Standard Dry 20.021 20.012 20.185 29.118 36.035 36.870 20.073 34.007

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.74 30.74 30.74 30.66 30.58 30.64 30.74 30.63

Water vapor in Stack Gas Percent 13.1 12.5 11.9 8.5 10.8 9.5 12.5 9.6

Average Stack Gas Velocity Feet per second 49.6 50.3 49.3 50.2 52.1 48.9 49.7 50.4

Stack Gas Flow Rate Actual Cubic 214,239 217,184 213,105 218,027 226,160 212,103 214,843 218,764

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 100,021 101,068 99,371 108,152 112,951 106,498 100,153 109,200

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 86,886 88,423 87,568 98,954 100,704 96,383 87,626 98,680

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 6,508 6,623 6,559 7,412 7,543 7,219 6,563 7,391

Per Minute

Particulate Concentration Grains per Standard 2.898 3.263 3.371 0.018 0.020 0.011 3.177 0.016 99.49

 Dry Cubic Foot

Particulate Concentration Grains per Actual 1.175 1.328 1.385 0.008 0.009 0.005 1.296 0.007 99.43

 Cubic Foot

Particulate Emission Rate Pounds per Hour 2,157.9 2,472.8 2,530.1 15.5 17.0 9.1 2,386.9 13.9 99.42

Particulate Emission Rate Pounds per Million 5.159 5.809 6.002 0.037 0.040 0.022 5.657 0.033 99.42

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 418 426 422 418 426 422 422 422

Part Conc. 50% Excess Air Grains per Standard 2.449 2.758 2.850 0.018 0.019 0.010 2.686 0.016

 Dry Cubic Foot

Excess Air Percent 27 27 27 46 45 40 27 44

Particulate Concentration Grains per Standard Dry 2.279 2.566 2.651 0.016 0.018 0.010 2.499 0.015 99.42

 Cubic Foot @ 8% O2

Particulate Concentration Grains per Standard Dry 1.926 2.168 2.240 0.014 0.015 0.008 2.112 0.012 99.42

 Cubic Foot @ 10% O2

Isokinetic Rate Percent 100.5 98.7 100.6 87.2 84.4 90.3 100.0 87.3

Post Test Meter Correction Check dimensionless 1.02 1.04 1.02 0.96 0.95 0.94 1.03 0.95

Percent Difference Allowed 5% Average 4.2 5.8 4.1 3.1 2.1 1.5 4.7 2.2

TABLE II. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 4

SIDE B
ATTACHMENT 54 - Crist Report 54 Test Results

2008 SO2 Emissions Test

Crist Unit 5

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LB MMBTU/HR

3 80 94800 10952 809

4 80 85400 10952 802

5 80 86600 10952 813

1.063

Time Time RM-6C (SO2)

Started Stopped lbs/mmBtu

4/9/08 9:08 4/9/08 10:08 1.077

4/9/08 6:06 4/9/08 7:06 1.060

4/9/08 7:34 4/9/08 8:34 1.052
ATTACHMENT 55 - Crist Report 55 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 4/9/2008 4/9/2008 4/9/2008

Sampling Time -Start Military 0606 0734 0908

Sampling Time -Stop Military 0716 0842 1018

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.15 0.15 0.15

Barometric Pressure Inches Mercury 30.24 30.24 30.24

Standard Orifice Pressure H@ Inches Water 1.939 1.939 1.939

Meter Correction Factor dimensionless 0.981 0.981 0.981

Oxygen Concentration Mole Percent O2 7.5 7.5 7.5

Carbon Dioxide Concentration Mole Percent CO2 12.0 12.0 12.5

Volume of Gas Metered Actual Cubic Feet 39.955 41.658 42.166

Volume of Water Collected Milliliters 82.8 89.1 66.4

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.228 0.226 0.228

Weight of Solids Collected Milligrams 19.3 20.2 5.1

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8129 0.8613 0.8672

Average Orifice Pressure (H) Inches Water 1.3 1.4 1.5

Average Stack Temperature Degrees F 279 281 282

Average Meter Temperature Degrees F 66 70 72

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 39.867 41.336 41.668 40.957

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.22 30.22 30.30 30.25

Water vapor in Stack Gas Percent 8.9 9.2 7.0 8.4

Average Stack Gas Velocity Feet per second 53.4 56.7 56.8 55.7

Stack Gas Flow Rate Actual Cubic 285,836 303,549 303,995 297,794

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 206,516 218,565 218,646 214,576

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 188,125 198,432 203,390 196,649

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,091 14,863 15,234 14,729

Per Minute

Particulate Concentration Grains per Standard 0.007 0.008 0.002 0.006

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.005 0.005 0.001 0.004

 Cubic Foot

Particulate Emission Rate Pounds per Hour 12.0 12.8 3.3 9.4

Particulate Emission Rate Pounds per Million 0.016 0.016 0.004 0.012

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 740 781 800 774

Isokinetic Rate Percent 104.1 104.1 100.6 103.0

Post Test Meter Correction Check dimensionless 0.96 0.97 0.98 0.97

Percent Difference Allowed 5% Average -1.8 -1.2 0.3 -0.9

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 5 SOOT BLOWING

Wednesday, April 09, 2008
ATTACHMENT 56 - Crist Report 56 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 4/9/2008 4/9/2008 4/9/2008

Sampling Time -Start Military 1148 1407 1534

Sampling Time -Stop Military 1256 1514 1641

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.10 0.10 0.10

Barometric Pressure Inches Mercury 30.21 30.21 30.21

Standard Orifice Pressure H@ Inches Water 1.939 1.939 1.939

Meter Correction Factor dimensionless 0.981 0.981 0.981

Oxygen Concentration Mole Percent O2 8.0 7.0 7.5

Carbon Dioxide Concentration Mole Percent CO2 12.5 12.0 11.5

Volume of Gas Metered Actual Cubic Feet 41.545 40.424 39.398

Volume of Water Collected Milliliters 82.1 87.1 66.9

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.228 0.226 0.226

Weight of Solids Collected Milligrams 11.5 4.3 6.7

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8484 0.8336 0.8200

Average Orifice Pressure (H) Inches Water 1.4 1.3 1.2

Average Stack Temperature Degrees F 282 284 284

Average Meter Temperature Degrees F 72 73 74

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 41.004 39.802 38.743 39.849

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.32 30.20 30.14 30.22

Water vapor in Stack Gas Percent 8.6 9.3 7.5 8.5

Average Stack Gas Velocity Feet per second 55.8 55.1 54.0 55.0

Stack Gas Flow Rate Actual Cubic 298,448 294,598 289,023 294,023

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 214,481 211,216 207,114 210,937

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 196,008 191,491 191,545 193,015

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,681 14,343 14,347 14,457

Per Minute

Particulate Concentration Grains per Standard 0.004 0.002 0.003 0.003

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.003 0.001 0.002 0.002

 Cubic Foot

Particulate Emission Rate Pounds per Hour 7.3 2.7 4.4 4.8

Particulate Emission Rate Pounds per Million 0.010 0.003 0.006 0.006

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 742 781 753 759

Isokinetic Rate Percent 102.8 103.9 101.1 102.6

Post Test Meter Correction Check dimensionless 0.97 0.96 0.96 0.96

Percent Difference Allowed 5% Average -1.6 -1.8 -2.5 -1.9

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 5 STEADY STATE

Wednesday, April 09, 2008
ATTACHMENT 57 - Crist Report 57 Test Results

Inlet Inlet Inlet Outlet Outlet Outlet

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/15/2008 5/15/2008 5/15/2008 5/15/2008 5/15/2008 5/15/2008

Sampling Time -Start Military 0955 1148 1325 0955 1150 1325

Sampling Time -Stop Military 1035 1228 1405 1055 1250 1425

Number of Ports dimensionless 4 4 4 8 8 8

Number of Points per Port dimensionless 5 5 5 3 3 3

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -5.00 -5.00 -5.00 -7.00 -7.00 -7.00

Barometric Pressure Inches Mercury 29.92 29.92 29.92 29.92 29.92 29.92

Standard Orifice Pressure DH@ Inches Water 2.258 2.258 2.258 1.939 1.939 1.939

Meter Correction Factor dimensionless 0.982 0.982 0.982 0.981 0.981 0.981

Oxygen Concentration Mole Percent O2 7.00 7.00 7.00 7.00 6.00 6.00

Carbon Dioxide Concentration Mole Percent CO2 12.0 12.0 12.0 13.0 14.0 14.0

Volume of Gas Metered Actual Cubic Feet 23.135 26.205 25.160 32.395 31.300 30.235

Volume of Water Collected Milliliters 53 60 60 65 59 58

Sampling Time Minutes 40 40 40 60 60 60

Nozzle Diameter Inches 0.292 0.310 0.292 0.275 0.275 0.275

Weight of Solids Collected Milligrams 3186.6 3542.5 5056.9 23.3 40.3 28.7

Area of Stack Square Feet 72.000 72.000 72.000 72.330 72.330 72.330

Avg. Sqr. Root Velocity Pressure Inches Water 0.5805 0.5827 0.5827 0.5591 0.5203 0.5206

Average Orifice Pressure (DH) Inches Water 1.4 1.7 1.5 1.0 0.9 0.8

Average Stack Temperature Degrees F 682 684 681 631 626 626

Average Meter Temperature Degrees F 118 124 108 88 88 81

CALCULATIONS A SIDE A SIDE

INLET OUTLET Efficiency

RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 AVERAGE AVERAGE

Volume of Gas Sampled Standard Dry 20.820 23.386 23.050 30.710 29.676 29.019 22.419 29.802

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.20 30.20 30.20 30.36 30.48 30.48 30.20 30.44

Water vapor in Stack Gas Percent 10.7 10.8 10.9 9.1 8.6 8.6 10.8 8.7

Average Stack Gas Velocity Feet per second 48.2 48.4 48.4 45.2 41.9 41.9 48.3 43.0

Stack Gas Flow Rate Actual Cubic 208,249 209,257 209,012 196,209 181,692 181,786 208,839 186,562

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 95,047 95,336 95,504 93,333 86,776 86,837 95,296 88,982

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 84,877 85,063 85,080 84,877 79,350 79,370 85,007 81,199

 Feet Per Minute

Particulate Concentration Grains per Standard 2.36 2.33 3.38 0.012 0.021 0.015 2.689 0.016 99.41

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.961 0.948 1.375 0.005 0.009 0.007 1.095 0.007 99.37

 Cubic Foot

Particulate Emission Rate Pounds per Hour 1,714.8 1,700.9 2,463.8 8.5 14.2 10.4 1,959.8 11.0 99.44

Particulate Emission Rate Pounds per Million 4.952 4.901 7.097 0.025 0.041 0.030 5.650 0.032 99.44

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 346 347 347 346 347 347 347 347

Isokinetic Rate Percent 94.9 94.4 104.8 105.7 109.3 106.8 98.1 107.3

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

CRIST UNIT 5 HOT SIDE PRECIPITATOR - A SIDE INLET AND OUTLET

Thursday, May 15, 2008
ATTACHMENT 58 - Crist Report 58 Test Results

Inlet Inlet Inlet Outlet Outlet Outlet

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/15/2008 5/15/2008 5/15/2008 5/15/2008 5/15/2008 5/15/2008

Sampling Time -Start Military 0955 1148 1325 0955 1150 1325

Sampling Time -Stop Military 1035 1228 1405 1055 1250 1425

Number of Ports dimensionless 4 4 4 8 8 8

Number of Points per Port dimensionless 5 5 5 3 3 3

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -5.00 -5.00 -5.00 -7.00 -7.00 -7.00

Barometric Pressure Inches Mercury 29.92 29.92 29.92 29.92 29.92 29.92

Standard Orifice Pressure DH@ Inches Water 1.858 1.858 1.858 2.211 2.211 2.211

Meter Correction Factor dimensionless 0.978 0.978 0.978 0.927 0.927 0.927

Oxygen Concentration Mole Percent O2 7.00 7.00 7.00 7.50 6.00 6.50

Carbon Dioxide Concentration Mole Percent CO2 12.00 12.00 13.00 13.00 14.50 14.50

Volume of Gas Metered Actual Cubic Feet 32.830 25.700 21.400 34.540 34.048 33.365

Volume of Water Collected Milliliters 79 63 52 50 60 61

Sampling Time Minutes 40 40 40 60 60 60

Nozzle Diameter Inches 0.328 0.286 0.270 0.278 0.278 0.278

Weight of Solids Collected Milligrams 3224.3 3065.9 3059.8 23.3 36.7 21.8

Area of Stack Square Feet 72.000 72.000 72.000 72.330 72.330 72.330

Avg. Sqr. Root Velocity Pressure Inches Water 0.6136 0.6011 0.6058 0.5970 0.5409 0.5633

Average Orifice Pressure (DH) Inches Water 2.3225 1.181 0.963 1.2 1.1 1.1

Average Stack Temperature Degrees F 661 656 661 594 621 619

Average Meter Temperature Degrees F 97 100 91 84 84 78

Inlet Inlet Inlet Outlet Outlet Outlet Inlet Outlet Efficiency

RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 AVERAGE AVERAGE

Volume of Gas Sampled Standard Dry 30.621 23.774 20.116 31.190 30.698 30.443 24.837 30.777

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.20 30.20 30.36 30.38 30.56 30.58 30.25 30.51

Water vapor in Stack Gas Percent 10.8 11.1 10.8 7.0 8.4 8.6 10.9 8.0

Average Stack Gas Velocity Feet per second 50.5 49.4 49.7 47.2 43.4 45.1 49.9 45.2

Stack Gas Flow Rate Actual Cubic 218,142 213,344 214,801 204,982 188,173 195,806 215,429 196,320

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 101,432 99,664 99,923 100,904 90,269 94,101 100,340 95,091

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 90,449 88,611 89,084 93,824 82,664 85,991 89,381 87,493

 Feet Per Minute

Particulate Concentration Grains per Standard 1.62 1.99 2.34 0.012 0.018 0.011 1.983 0.014 99.31

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.672 0.825 0.971 0.005 0.008 0.005 0.823 0.006 99.26

 Cubic Foot

Particulate Emission Rate Pounds per Hour 1,257.2 1,508.4 1,788.6 9.3 13.0 8.1 1,518.1 10.1 99.33

Particulate Emission Rate Pounds per Million 3.406 4.172 4.921 0.025 0.036 0.022 4.166 0.028 99.33

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 369 362 363 369 362 363 365 365

Isokinetic Rate Percent 103.8 108.2 102.2 95.1 106.2 101.2 104.8 100.8

TABLE II. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

CRIST UNIT 5 HOT SIDE PRECIPITATOR - B SIDE INLET & OUTLET

Thursday, May 15, 2008
ATTACHMENT 59 - Crist Report 59 Test Results

2008 SO2 Emissions Test

Crist Unit 6

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LB MMBTU/HR

3 320 272880 11467 3129

4 320 287500 11467 3243

5 318 278040 11467 3188

1.049

Time Time RM-6C (SO2)

Started Stopped lbs/mmBtu

5/20/08 11:10 5/20/08 12:10 1.015

5/20/08 8:12 5/20/08 9:12 1.066

5/20/08 9:42 5/20/08 10:42 1.066
ATTACHMENT 60 - Crist Report 60 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/20/2008 5/20/2008 5/20/2008

Sampling Time -Start Military 0912 1041 1210

Sampling Time -Stop Military 1016 1143 1313

Number of Ports dimensionless 6 6 6

Number of Points per Port dimensionless 5 5 5

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.60 0.60 0.60

Barometric Pressure Inches Mercury 29.98 29.98 29.98

Standard Orifice Pressure H@ Inches Water 2.211 2.211 2.211

Meter Correction Factor dimensionless 0.927 0.927 0.927

Oxygen Concentration Mole Percent O2 8.5 9.0 8.5

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.0 11.5

Volume of Gas Metered Actual Cubic Feet 53.600 50.475 52.447

Volume of Water Collected Milliliters 110.0 94.0 104.0

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.216 0.210 0.212

Weight of Solids Collected Milligrams 10.7 5.1 9.3

Area of Stack Square Feet 270.000 270.000 270.000

Avg. Sqr. Root Velocity Pressure Inches Water 1.2868 1.2923 1.3168

Average Orifice Pressure (H) Inches Water 3.0 2.6 2.7

Average Stack Temperature Degrees F 338 338 340

Average Meter Temperature Degrees F 82 83 85

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 48.855 45.910 47.494 47.419

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.18 30.12 30.18 30.16

Water vapor in Stack Gas Percent 9.6 8.8 9.3 9.2

Average Stack Gas Velocity Feet per second 88.4 88.8 90.6 89.2

Stack Gas Flow Rate Actual Cubic 1,432,541 1,437,963 1,466,983 1,445,829

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 950,904 954,105 971,372 958,793

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 859,783 870,235 880,606 870,208

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 64,398 65,181 65,957 65,179

Per Minute

Particulate Concentration Grains per Standard 0.003 0.002 0.003 0.003

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.002 0.001 0.002 0.002

 Cubic Foot

Particulate Emission Rate Pounds per Hour 24.9 12.8 22.8 20.1

Particulate Emission Rate Pounds per Million 0.008 0.004 0.007 0.006

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 3,130 3,040 3,205 3,125

Isokinetic Rate Percent 100.5 98.7 99.0 99.4

Post Test Meter Correction Check dimensionless 0.96 0.96 0.95 0.96

Percent Difference Allowed 5% Average 3.4 3.2 2.0 2.9

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

SOOT BLOW TEST
ATTACHMENT 61 - Crist Report 61 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/20/2008 5/20/2008 5/20/2008

Sampling Time -Start Military 1435 1607 1725

Sampling Time -Stop Military 1538 1709 1830

Number of Ports dimensionless 6 6 6

Number of Points per Port dimensionless 5 5 5

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.60 0.60 0.60

Barometric Pressure Inches Mercury 29.98 29.98 29.98

Standard Orifice Pressure H@ Inches Water 2.211 2.211 2.211

Meter Correction Factor dimensionless 0.927 0.927 0.927

Oxygen Concentration Mole Percent O2 8.0 8.5 8.5

Carbon Dioxide Concentration Mole Percent CO2 11.5 11.0 11.0

Volume of Gas Metered Actual Cubic Feet 53.725 52.765 52.579

Volume of Water Collected Milliliters 95.0 89.0 105.0

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.215 0.214 0.214

Weight of Solids Collected Milligrams 7.5 20.1 56.6

Area of Stack Square Feet 270.000 270.000 270.000

Avg. Sqr. Root Velocity Pressure Inches Water 1.3040 1.3002 1.2996

Average Orifice Pressure (H) Inches Water 2.8 2.8 2.7

Average Stack Temperature Degrees F 339 338 338

Average Meter Temperature Degrees F 86 86 85

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 48.575 47.712 47.643 47.977

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.16 30.10 30.10 30.12

Water vapor in Stack Gas Percent 8.4 8.1 9.4 8.6

Average Stack Gas Velocity Feet per second 89.5 89.2 89.4 89.4

Stack Gas Flow Rate Actual Cubic 1,449,517 1,444,750 1,448,445 1,447,571

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 961,048 958,928 960,979 960,319

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 880,034 881,529 870,660 877,408

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 65,915 66,026 65,212 65,718

Per Minute

Particulate Concentration Grains per Standard 0.002 0.006 0.018 0.009

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.004 0.011 0.005

 Cubic Foot

Particulate Emission Rate Pounds per Hour 17.9 49.0 136.5 67.8

Particulate Emission Rate Pounds per Million 0.005 0.015 0.043 0.021

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 3,332 3,209 3,169 3,237

Isokinetic Rate Percent 98.5 97.5 98.6 98.2

Post Test Meter Correction Check dimensionless 0.94 0.95 0.95 0.94

Percent Difference Allowed 5% Average 1.3 2.2 2.0 1.8

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

STEADY STATE
ATTACHMENT 62 - Crist Report 62 Test Results

2008 SO2 Emissions Test

Crist Unit 7

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LB MMBTU/HR

3 500 423480 11264 4770

4 500 404780 11985 4851

5 500 418180 11985 4850

1.057

Time Time RM-6C (SO2)

Started Stopped lbs/mmBtu

5/13/08 9:19 5/13/08 10:19 1.043

5/13/08 6:27 5/13/08 7:27 1.069

5/13/08 7:56 5/13/08 8:56 1.059
ATTACHMENT 63 - Crist Report 63 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/13/2008 5/13/2008 5/13/2008

Sampling Time -Start Military 0727 0856 1017

Sampling Time -Stop Military 0838 1004 1124

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.75 0.75 0.75

Barometric Pressure Inches Mercury 30.06 30.06 30.06

Standard Orifice Pressure H@ Inches Water 2.211 2.211 2.211

Meter Correction Factor dimensionless 0.927 0.927 0.927

Oxygen Concentration Mole Percent O2 7.00 7.50 7.00

Carbon Dioxide Concentration Mole Percent CO2 13.0 12.5 13.0

Volume of Gas Metered Actual Cubic Feet 43.570 44.045 42.358

Volume of Water Collected Milliliters 58 58 71

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.187 0.188 0.186

Weight of Solids Collected Milligrams 28.6 33.6 13.2

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3705 1.3656 1.3351

Average Orifice Pressure (H) Inches Water 2.0 2.0 1.9

Average Stack Temperature Degrees F 324 331 339

Average Meter Temperature Degrees F 82 83 85

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 39.770 40.073 38.388 39.410

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.36 30.30 30.36 30.34

Water vapor in Stack Gas Percent 6.4 6.4 8.0 6.9

Average Stack Gas Velocity Feet per second 92.3 92.5 91.1 92.0

Stack Gas Flow Rate Actual Cubic 2,029,307 2,032,393 2,002,437 2,021,379

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,375,017 1,365,436 1,331,111 1,357,188

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,286,689 1,278,346 1,224,508 1,263,181

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 96,373 95,748 91,716 94,612

Per Minute

Particulate Concentration Grains per Standard 0.011 0.013 0.005 0.010

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.007 0.008 0.003 0.006

 Cubic Foot

Particulate Emission Rate Pounds per Hour 122.1 141.5 55.6 106.4

Particulate Emission Rate Pounds per Million 0.023 0.028 0.011 0.021

Allowale Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 5,250 5,028 4,996 5,091

Isokinetic Rate Percent 98.9 99.2 101.4 99.8

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 7

SOOT BLOWING OPERATIONS
ATTACHMENT 64 - Crist Report 64 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/14/2008 5/14/2008 5/14/2008

Sampling Time -Start Military 0840 1015 1133

Sampling Time -Stop Military 0944 1120 1238

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.75 0.75 0.75

Barometric Pressure Inches Mercury 30.02 30.02 30.02

Standard Orifice Pressure H@ Inches Water 2.211 2.211 2.211

Meter Correction Factor dimensionless 0.927 0.927 0.927

Oxygen Concentration Mole Percent O2 7.00 7.00 7.50

Carbon Dioxide Concentration Mole Percent CO2 13.0 13.0 12.5

Volume of Gas Metered Actual Cubic Feet 43.745 44.392 43.945

Volume of Water Collected Milliliters 60 74 76

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.186 0.186 0.183

Weight of Solids Collected Milligrams 13.8 24.2 23.2

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.4101 1.4189 1.4363

Average Orifice Pressure (H) Inches Water 2.0 2.0 2.0

Average Stack Temperature Degrees F 335 339 343

Average Meter Temperature Degrees F 77 82 84

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 40.178 40.444 39.887 40.170

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.36 30.36 30.30 30.34

Water vapor in Stack Gas Percent 6.6 7.9 8.2 7.6

Average Stack Gas Velocity Feet per second 95.7 96.9 98.5 97.0

Stack Gas Flow Rate Actual Cubic 2,104,177 2,128,709 2,163,729 2,132,205

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,404,560 1,413,819 1,429,738 1,416,039

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,312,315 1,301,710 1,312,063 1,308,696

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 98,292 97,498 98,274 98,021

Per Minute

Particulate Concentration Grains per Standard 0.005 0.009 0.009 0.008

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.003 0.006 0.005 0.005

 Cubic Foot

Particulate Emission Rate Pounds per Hour 59.5 102.8 100.7 87.7

Particulate Emission Rate Pounds per Million 0.011 0.019 0.020 0.017

Allowale Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 5,355 5,311 5,161 5,276

Isokinetic Rate Percent 99.0 100.5 101.6 100.4

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 7

STEADY STATE OPERATIONS
ATTACHMENT 65 - Crist Report 65 Test Results

2009 SO2 Emissions Test

Run Unit FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LB MMBTU/HR

Number Load

1 82 74390 11380 847

2 82 72593 11380 826

3 82 72842 11380 829

0.757 AVERAGE= 833.9

Started Stopped lbs/mmBtu

Crist Unit 4

Time Time RM-6C (SO2)

2/3/09 11:05 2/3/09 12:05 0.766

2/3/09 8:00 2/3/09 9:00 0.750

2/3/09 9:43 2/3/09 10:43 0.756
ATTACHMENT 66 - Crist Report 66 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 2/3/2009 2/3/2009 9/25/2008

Sampling Time -Start Military 1255 1417 1537

Sampling Time -Stop Military 1401 1523 1644

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.40 0.40 0.40

Barometric Pressure Inches Mercury 30.22 30.22 30.22

Standard Orifice Pressure DH@ Inches Water 1.858 1.858 1.858

Meter Correction Factor dimensionless 0.978 0.978 0.978

Oxygen Concentration Mole Percent O2 6.9 6.0 6.0

Carbon Dioxide Concentration Mole Percent CO2 13.0 12.5 12.0

Volume of Gas Metered Actual Cubic Feet 36.310 36.535 35.400

Volume of Water Collected Milliliters 69.0 72.0 62.0

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.216 0.216 0.217

Weight of Solids Collected Milligrams 4.3 5.3 4.0

Area of Stack Square Feet 89.168 89.168 89.168

Avg. Sqr. Root Velocity Pressure Inches Water 0.8447 0.8453 0.8144

Average Orifice Pressure (DH) Inches Water 1.1 1.1 1.0

Average Stack Temperature Degrees F 288 289 289

Average Meter Temperature Degrees F 57 63 62

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 36.730 36.512 35.465 36.236

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.36 30.24 30.16 30.25

Water vapor in Stack Gas Percent 8.1 8.5 7.6 8.1

Average Stack Gas Velocity Feet per second 55.7 55.9 53.8 55.1

Stack Gas Flow Rate Actual Cubic 297,885 298,993 287,806 294,895

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 212,441 213,044 205,219 210,235

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 195,183 194,949 189,616 193,249

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,619 14,602 14,202 14,474

Per Minute

Particulate Concentration Grains per Standard 0.002 0.002 0.002 0.002

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.001 0.001 0.001

 Cubic Foot

Particulate Emission Rate Pounds per Hour 3.0 3.7 2.8 3.2

Particulate Emission Rate Pounds per Million 0.004 0.004 0.003 0.004

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 802 853 829 828

Isokinetic Rate Percent 103.0 102.5 101.4 102.3

Post Test Meter Correction Check dimensionless 0.97 0.97 0.97 0.97

Percent Difference Allowed 5% Average -1.2 -1.0 -0.9 -1.0

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 4

SOOT BLOWING
ATTACHMENT 67 - Crist Report 67 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 2/3/2009 2/3/2009 9/25/2008

Sampling Time -Start Military 0800 0943 1105

Sampling Time -Stop Military 0926 1050 1214

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 0.40 0.40 0.40

Barometric Pressure Inches Mercury 30.22 30.22 30.22

Standard Orifice Pressure DH@ Inches Water 1.858 1.858 1.858

Meter Correction Factor dimensionless 0.978 0.978 0.978

Oxygen Concentration Mole Percent O2 7.5 6.1 6.9

Carbon Dioxide Concentration Mole Percent CO2 14.0 12.0 12.5

Volume of Gas Metered Actual Cubic Feet 34.300 36.675 36.620

Volume of Water Collected Milliliters 51.0 74.0 68.0

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.220 0.220 0.217

Weight of Solids Collected Milligrams 3.9 9.7 24.6

Area of Stack Square Feet 89.168 89.168 89.168

Avg. Sqr. Root Velocity Pressure Inches Water 0.7581 0.8154 0.8383

Average Orifice Pressure (DH) Inches Water 1.0 1.1 1.1

Average Stack Temperature Degrees F 281 285 285

Average Meter Temperature Degrees F 46 49 52

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 35.458 37.654 37.411 36.841

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.54 30.16 30.28 30.33

Water vapor in Stack Gas Percent 6.3 8.5 7.9 7.6

Average Stack Gas Velocity Feet per second 49.4 53.8 55.2 52.8

Stack Gas Flow Rate Actual Cubic 264,226 287,889 295,081 282,399

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 190,369 206,382 211,537 202,763

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 178,298 188,907 194,865 187,357

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 13,355 14,149 14,595 14,033

Per Minute

Particulate Concentration Grains per Standard 0.002 0.004 0.010 0.005

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.003 0.007 0.003

 Cubic Foot

Particulate Emission Rate Pounds per Hour 2.6 6.4 16.9 8.6

Particulate Emission Rate Pounds per Million 0.004 0.008 0.021 0.011

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 701 821 801 774

Isokinetic Rate Percent 104.9 105.2 104.1 104.7

Post Test Meter Correction Check dimensionless 0.96 0.96 0.96 0.96

Percent Difference Allowed 5% Average -2.2 -1.9 -1.9 -2.0

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST, UNIT 4

STEADY STATE OPERATIONS
ATTACHMENT 68 - Crist Report 68 Test Results

2009 SO2 Emissions Test

Crist Unit 5

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LB MMBTU/HR

1 80 70499 11232 792

2 80 70630 11232 793

3 80 71195 11232 800

1.594 AVERAGE= 794.9

Time Time RM-6C (SO2)

Started Stopped lbs/mmBtu

2/17/09 10:30 2/17/09 11:30 1.546

2/17/09 7:05 2/17/09 8:05 1.628

2/17/09 8:53 2/17/09 9:53 1.607
ATTACHMENT 69 - Crist Report 69 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 2/17/2009 2/17/2009 2/17/2009

Sampling Time -Start Military 1305 1442 1618

Sampling Time -Stop Military 1410 1549 1724

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.45 -0.45 -0.45

Barometric Pressure Inches Mercury 30.15 30.15 30.15

Standard Orifice Pressure DH@ Inches Water 1.907 1.907 1.907

Meter Correction Factor dimensionless 0.980 0.980 0.980

Oxygen Concentration Mole Percent O2 7.0 6.0 6.0

Carbon Dioxide Concentration Mole Percent CO2 11.5 12.0 12.0

Volume of Gas Metered Actual Cubic Feet 41.839 44.373 44.830

Volume of Water Collected Milliliters 73.0 71.6 79.0

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.234 0.238 0.239

Weight of Solids Collected Milligrams 4.2 4.4 5.0

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8488 0.8592 0.8584

Average Orifice Pressure (DH) Inches Water 1.4 1.6 1.6

Average Stack Temperature Degrees F 301 303 305

Average Meter Temperature Degrees F 63 64 65

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 41.893 44.308 44.743 43.648

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.12 30.16 30.16 30.15

Water vapor in Stack Gas Percent 7.6 7.1 7.7 7.4

Average Stack Gas Velocity Feet per second 56.7 57.4 57.4 57.2

Stack Gas Flow Rate Actual Cubic 303,297 306,902 307,236 305,812

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 211,657 213,647 213,547 212,950

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 195,613 198,545 197,161 197,106

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,651 14,871 14,767 14,763

Per Minute

Particulate Concentration Grains per Standard 0.002 0.002 0.002 0.002

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.001 0.001 0.001

 Cubic Foot

Particulate Emission Rate Pounds per Hour 2.6 2.6 2.9 2.7

Particulate Emission Rate Pounds per Million 0.003 0.003 0.003 0.003

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 798 868 862 843

Excess Air Percent 48 38 38 42

Isokinetic Rate Percent 99.9 100.6 101.4 100.6

Post Test Meter Correction Check dimensionless 0.97 0.96 0.95 0.96

Percent Difference Allowed 5% Average -1.3 -2.2 -2.5 -2.0

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 5

SOOT BLOWING OPERATIONS
ATTACHMENT 70 - Crist Report 70 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 2/17/2009 2/17/2009 2/17/2009

Sampling Time -Start Military 0705 0853 1030

Sampling Time -Stop Military 0813 1001 1137

Number of Ports dimensionless 4 4 4

Number of Points per Port dimensionless 8 8 8

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water -0.40 -0.40 -0.45

Barometric Pressure Inches Mercury 30.15 30.15 30.15

Standard Orifice Pressure DH@ Inches Water 1.907 1.907 1.907

Meter Correction Factor dimensionless 0.980 0.980 0.980

Oxygen Concentration Mole Percent O2 8.0 7.5 7.5

Carbon Dioxide Concentration Mole Percent CO2 11.5 12.0 12.5

Volume of Gas Metered Actual Cubic Feet 42.537 40.948 41.007

Volume of Water Collected Milliliters 62.7 73.9 61.2

Sampling Time Minutes 64 64 64

Nozzle Diameter Inches 0.237 0.233 0.235

Weight of Solids Collected Milligrams 5.3 5.3 7.4

Area of Stack Square Feet 89.150 89.150 89.150

Avg. Sqr. Root Velocity Pressure Inches Water 0.8406 0.8386 0.8303

Average Orifice Pressure (DH) Inches Water 1.5 1.4 1.4

Average Stack Temperature Degrees F 294 297 300

Average Meter Temperature Degrees F 49 54 61

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 43.755 41.655 41.183 42.198

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.16 30.22 30.30 30.23

Water vapor in Stack Gas Percent 6.3 7.7 6.5 6.9

Average Stack Gas Velocity Feet per second 55.7 55.8 55.1 55.5

Stack Gas Flow Rate Actual Cubic 297,962 298,395 294,917 297,091

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 209,933 209,475 206,250 208,553

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 196,668 193,330 192,766 194,255

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 14,730 14,480 14,438 14,550

Per Minute

Particulate Concentration Grains per Standard 0.002 0.002 0.003 0.002

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.001 0.001 0.002 0.001

 Cubic Foot

Particulate Emission Rate Pounds per Hour 3.1 3.2 4.6 3.7

Particulate Emission Rate Pounds per Million 0.004 0.004 0.006 0.005

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 745 760 758 754

Isokinetic Rate Percent 101.1 101.3 98.8 100.4

Post Test Meter Correction Check dimensionless 0.95 0.96 0.96 0.96

Percent Difference Allowed 5% Average -3.2 -2.3 -1.7 -2.4

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 5

STEADY STATE OPERATIONS
ATTACHMENT 71 - Crist Report 71 Test Results

2009 SO2 Emissions Test

Crist Unit 6

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LBMMBTU/HR

1 313 270000 11779 3180

2 313 274000 11779 3227

3 314 276000 11779 3251

1.772 AVERAGE= 3219.6

Time Time RM-6C (SO2)

Started Stopped lbs/mmBtu

5/11/09 13:30 5/11/09 14:30 1.845

5/11/09 10:35 5/11/09 11:35 1.711

5/11/09 12:05 5/11/09 13:05 1.759
ATTACHMENT 72 - Crist Report 72 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3

Date Month/Day/Year 5/11/2009 5/11/2009 5/11/2009 5/11/2009 5/11/2009 5/11/2009

Sampling Time -Start Military 1135 1305 1430 1135 1305 1430

Sampling Time -Stop Military 1235 1405 1530 1235 1405 1530

Number of Ports dimensionless 5 5 5 5 5 5

Number of Points per Port dimensionless 6 6 6 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -24.00 -24.00 -24.00 -24.50 -24.50 -24.50

Barometric Pressure Inches Mercury 29.97 29.97 29.97 29.97 29.97 29.97

Standard Orifice Pressure H@ Inches Water 2.211 2.211 2.211 2.040 2.040 2.040

Meter Correction Factor dimensionless 0.927 0.927 0.927 0.975 0.975 0.975

Oxygen Concentration Mole Percent O2 8.50 5.50 6.00 7.00 5.00 5.50

Carbon Dioxide Concentration Mole Percent CO2 11.0 10.5 11.0 11.5 10.5 11.0

Volume of Gas Metered Actual Cubic Feet 51.280 50.021 47.120 48.217 49.479 51.032

Volume of Water Collected Milliliters 92.4 77.1 67.6 73.9 83.3 88.6

Sampling Time Minutes 60 60 60 60 60 60

Nozzle Diameter Inches 0.248 0.249 0.245 0.250 0.250 0.243

Weight of Solids Collected Milligrams 7.7 8.7 11.8 3.8 3.9 3.2

Area of Stack Square Feet 179.869 179.869 179.869 180.035 180.035 180.035

Avg. Sqr. Root Velocity Pressure Inches Water 0.8951 0.8729 0.8794 0.9209 0.9297 0.9414

Average Orifice Pressure (H) Inches Water 2.4 2.3 2.2 2.4 2.5 2.6

Average Stack Temperature Degrees F 310 314 314 320 321 320

Average Meter Temperature Degrees F 89 91 89 91 94 93

Calculations

Side A Side A Side A Side B Side B Side B Side A Side B Combined

RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 AVERAGE AVERAGE AVERAGE

Volume of Gas Sampled Standard Dry 46.098 44.769 42.279 45.431 46.325 47.930 44.382 46.562 90.944

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.10 29.90 30.00 30.12 29.88 29.98 30.00 29.99 30.00

Water vapor in Stack Gas Percent 8.6 7.5 7.0 7.1 7.8 8.0 7.7 7.6 7.7

0 0 0

Average Stack Gas Velocity Feet per second 62.3 61.0 61.3 64.3 65.3 66.0 61.5 65.2 63.4

Stack Gas Flow Rate Actual Cubic 672,076 657,803 661,074 694,693 705,703 713,086 663,651 704,494 1,368,145

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 434,600 422,951 424,963 442,788 448,961 454,453 427,505 448,734 876,239

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 397,131 391,237 395,219 411,297 413,926 418,076 394,529 414,433 808,962

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 29,745 29,304 29,602 30,806 31,003 31,314 29,550 31,041 60,591

Per Minute

Particulate Concentration Grains per Standard 0.003 0.003 0.004 0.001 0.001 0.001 0.003 0.001 0.002

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.002 0.002 0.003 0.001 0.001 0.001 0.002 0.001 0.001

 Cubic Foot

Particulate Emission Rate Pounds per Hour 8.8 10.0 14.6 4.5 4.6 3.7 11.1 4.3 15.4

Particulate Emission Rate Pounds per Million 0.006 0.006 0.008 0.003 0.002 0.002 0.007 0.002 0.005

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 1,446 1,769 1,729 1,678 1,932 1,890 1,648 1,833 3,481

Isokinetic Rate Percent 103.7 101.4 97.9 97.2 98.5 106.8 101.0 100.8

Post Test Meter Correction Check dimensionless 0.91 0.91 0.94 1.00 1.00 0.99 0.92 1.00

Percent Difference Allowed 5% Average -2.2 -1.5 1.5 2.9 2.9 1.7 -0.7 2.5

Combined Particulate Emission Rate Pounds per Million 0.004 0.004 0.005 0.005

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

SOOT BLOWING CONDITION
ATTACHMENT 73 - Crist Report 73 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3

Date Month/Day/Year5/12/2009 5/12/2009 5/12/2009 5/12/2009 5/12/2009 5/12/2009

Sampling Time -Start Military 0725 0855 1015 0725 0855 1015

Sampling Time -Stop Military 0825 0955 1115 0825 0955 1115

Number of Ports dimensionless 5 5 5 5 5 5

Number of Points per Port dimensionless 6 6 6 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780

Stack Static Pressure Inches Water -25.00 -25.00 -25.00 -24.50 -24.50 -24.50

Barometric Pressure Inches Mercury 30.02 30.02 30.02 30.02 30.02 30.02

Standard Orifice Pressure Inches Water 2.211 2.211 2.211 2.040 2.040 2.040

Meter Correction Factor dimensionless 0.927 0.927 0.927 0.975 0.975 0.975

Oxygen Concentration Mole Percent O2 7.50 7.50 7.00 7.00 6.00 6.00

Carbon Dioxide Concentration Mole Percent CO2 11.0 10.5 10.5 12.0 12.0 12.0

Volume of Gas Metered Actual Cubic Feet 49.721 52.226 52.237 44.247 49.089 50.179

Volume of Water Collected Milliliters 69.3 94.4 79.9 73.2 104.9 108.9

Sampling TimeMinutes 60 60 60 60 60 60

Nozzle Diameter Inches 0.245 0.248 0.249 0.240 0.250 0.250

Weight of Solids Collected Milligrams 36.4 6.3 7.7 13.7 5.5 5.5

Area of StackSquare Feet 179.869 179.869 179.869 180.035 180.035 180.035

Avg. Sqr. Root Velocity Pressure Inches Water 0.9002 0.9132 0.9095 0.9280 0.9403 0.9534

Average Orifice Pressure ( Inches Water 2.2 2.4 2.4 2.0 2.5 2.5

Average Stack Temperature Degrees F 295 300 303 310 312 314

Average Meter Temperature Degrees F 75 77 82 78 81 87

Calculations

Side A Side A Side A Side B Side B Side B Side A Side B Combined

RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 AVERAGE AVERAGE AVERAGE

Volume of Gas Sampled Standard Dry 45.935 48.048 47.630 42.668 47.160 47.709 47.204 45.846 93.050

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.06 29.98 29.96 30.20 30.16 30.16 30.00 30.17 30.09

Water vapor in Stack Gas Percent 6.6 8.5 7.3 7.5 9.5 9.7 7.5 8.9 8.2

0 0 0

Average Stack Gas Velocity Feet per second 61.9 63.2 63.0 64.3 65.6 66.6 62.7 65.5 64.1

Stack Gas Flow Rate Actual Cubic 667,611 682,502 679,722 694,814 708,185 719,270 676,612 707,423 1,384,034

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic439,465 446,802 443,211 449,047 456,740 462,770 443,159 456,186 899,345

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 410,327 408,980 410,776 415,496 413,451 417,872 410,028 415,606 825,634

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 30,733 30,633 30,767 31,121 30,968 31,299 30,711 31,129 61,840

Per Minute

Particulate Concentration Grains per Standard 0.012 0.002 0.002 0.005 0.002 0.002 0.006 0.003 0.004

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.008 0.001 0.002 0.003 0.001 0.001 0.003 0.002 0.003

 Cubic Foot

Particulate Emission Rate Pounds per Hour 42.9 7.1 8.8 17.6 6.4 6.4 19.6 10.1 29.7

Particulate Emission Rate Pounds per Million 0.027 0.004 0.005 0.010 0.004 0.003 0.012 0.006 0.009

 Btu (O2 F Factor)

Heat Input (O2 F Factor) Million Btu per Hour 1,614 1,609 1,676 1,695 1,808 1,828 1,633 1,777 3,410

Isokinetic RatePercent 102.5 105.0 102.8 98.1 100.4 100.5 103.4 99.6

Post Test Meter Correction Check dimensionless 0.89 0.89 0.90 1.00 0.99 1.00 0.89 1.00

Percent Difference Allowed 5% Average -3.6 -3.3 -2.8 2.4 1.9 2.1 -3.2 2.1

Combined Particulate Emission Rate Pounds per Million 0.018 0.004 0.004 0.009

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 6

STEADY STATE CONDITION
ATTACHMENT 74 - Crist Report 74 Test Results

Title of Run Date Start Time End Time Test Load

Avg. Econ 

Gas Outlet 

CO 

Avg. Econ 

Gas Outlet 

O2 

Avg. Econ 

Gas Outlet 

CO2 

Avg. Econ 

Gas Outlet 

Temp 

Military Military MW ppm % dry % dry DEGF 

Test 1 R1 7/21/2009 13:52 14:40 300.3 316 5.21 13.46 713

Test 1 R2 7/21/2009 15:51 16:40 300.8 294 5.27 13.36 723.4

Test 2 R1 7/22/2009 11:27 12:15 299.9 390 5.29 13.42 726.2

Test 2 R2 7/22/2009 12:16 13:05 299.9 397 5.27 13.42 729.2

Test 3 R1 7/23/2009 9:23 10:11 300 273 5.37 13.4 738.9

Test 3 R2 7/23/2009 10:17 11:05 299.9 296 5.3 13.42 739.5

Test 4 R1 7/23/2009 12:55 13:43 300.1 101 5.4 13.38 747.8

Test 4 R2 7/23/2009 13:46 14:36 300 121 5.39 13.37 748

Test 5 R1 7/23/2009 17:03 17:51 299.8 246 5.49 13.3 743.5

Test 5 R2 7/23/2009 17:52 18:40 299.9 252 5.5 13.3 746.7

Test 6 R1 7/24/2009 8:53 9:41 300 805 5.48 13.3 737.9

Test 6 R2 7/24/2009 12:00 12:48 300 1040 5.43 13.29 744.2

Tuning 1 7/28/2009 9:46 10:34 299.9 194 5.23 13.52 725.8

Tuning 2 7/28/2009 14:04 14:52 299.9 77 5.48 13.29 730.4

Tuning 3 7/28/2009 16:42 17:30 300.1 101 5.4 13.3 737.3

Test 7 R1 7/29/2009 10:48 11:46 300 134 5.61 13.32 725.7

Test 7 R2 7/29/2009 14:37 15:25 299.9 130 5.5 13.32 741.3

SCR Baseline Test Results Summary

Crist Unit 6
ATTACHMENT 75 - Crist Report 75 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 4/20/2009 4/20/2009 4/20/2009

Sampling Time -Start Military 1305 1438 1558

Sampling Time -Stop Military 1416 1545 1705

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.75 1.75 1.75

Barometric Pressure Inches Mercury 29.90 29.90 29.90

Standard Orifice Pressure DH@ Inches Water 2.040 2.040 2.040

Meter Correction Factor dimensionless 0.975 0.975 0.975

Oxygen Concentration Mole Percent O2 7.5 7.0 7.0

Carbon Dioxide Concentration Mole Percent CO2 12.0 12.0 11.5

Volume of Gas Metered Actual Cubic Feet 42.452 42.855 42.163

Volume of Water Collected Milliliters 72.0 67.0 67.9

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.187 0.187 0.186

Weight of Solids Collected Milligrams 10.4 13.7 10.4

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3974 1.3930 1.3824

Average Orifice Pressure (DH) Inches Water 2.1 2.0 2.0

Average Stack Temperature Degrees F 325 328 329

Average Meter Temperature Degrees F 99 98 98

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 39.271 39.687 39.076 39.345

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.22 30.20 30.12 30.18

Water vapor in Stack Gas Percent 7.9 7.4 7.6 7.6

Average Stack Gas Velocity Feet per second 94.8 94.7 94.2 94.6

Stack Gas Flow Rate Actual Cubic 2,084,102 2,080,461 2,069,328 2,077,964

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,407,073 1,398,080 1,388,894 1,398,016

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,295,290 1,295,161 1,283,884 1,291,445

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 97,017 97,008 96,163 96,729

Per Minute

Particulate Concentration Grains per Standard 0.0041 0.0053 0.0041 0.0045

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0025 0.0033 0.0025 0.0028

 Cubic Foot

Particulate Emission Rate Pounds per Hour 45.3 59.0 45.1 49.8

Particulate Emission Rate Pounds per Million 0.009 0.011 0.009 0.010

Allowable Btu (O2 F Factor) 0.1 0.1 0.1 0.1

Heat Input (O2 F Factor) Million Btu per Hour 5,095 5,285 5,238 5,206

Isokinetic Rate Percent 97.0 98.1 98.4 97.8

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 7

STEADY STATE OPERATIONS
ATTACHMENT 76 - Crist Report 76 Test Results

Title of Run RUN 1 RUN 2 RUN 3

Date Month/Day/Year 4/22/2009 4/22/2009 4/22/2009

Sampling Time -Start Military 0751 0911 1030

Sampling Time -Stop Military 0856 1015 1135

Number of Ports dimensionless 5 5 5

Number of Points per Port dimensionless 6 6 6

Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780

Stack Static Pressure Inches Water 1.85 1.85 1.85

Barometric Pressure Inches Mercury 30.05 30.05 30.05

Standard Orifice Pressure DH@ Inches Water 2.040 2.040 2.040

Meter Correction Factor dimensionless 0.975 0.975 0.975

Oxygen Concentration Mole Percent O2 6.5 6.5 6.0

Carbon Dioxide Concentration Mole Percent CO2 13.0 13.0 13.0

Volume of Gas Metered Actual Cubic Feet 40.163 39.905 41.825

Volume of Water Collected Milliliters 79.7 70.7 81.2

Sampling Time Minutes 60 60 60

Nozzle Diameter Inches 0.182 0.184 0.185

Weight of Solids Collected Milligrams 10.7 8.2 9.9

Area of Stack Square Feet 366.263 366.263 366.263

Avg. Sqr. Root Velocity Pressure Inches Water 1.3920 1.3410 1.3997

Average Orifice Pressure (DH) Inches Water 1.9 1.8 2.0

Average Stack Temperature Degrees F 305 313 319

Average Meter Temperature Degrees F 89 95 95

Calculations

RUN 1 RUN 2 RUN 3 AVERAGE

Volume of Gas Sampled Standard Dry 38.033 37.363 39.162 38.186

 Cubic Feet 

Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.34 30.34 30.32 30.33

Water vapor in Stack Gas Percent 9.0 8.2 8.9 8.7

Average Stack Gas Velocity Feet per second 93.0 90.0 94.4 92.5

Stack Gas Flow Rate Actual Cubic 2,044,702 1,977,251 2,075,611 2,032,521

 Feet Per Minute

Stack Gas Flow Rate Standard Wet Cubic 1,423,952 1,361,953 1,418,570 1,401,492

 Feet Per Minute

Stack Gas Flow Rate Standard Dry Cubic 1,296,108 1,250,567 1,292,431 1,279,702

 Feet Per Minute

Stack Gas Flow Rate Pounds of Dry Air 97,078 93,668 96,803 95,850

Per Minute

Particulate Concentration Grains per Standard 0.0043 0.0034 0.0039 0.0039

 Dry Cubic Foot

Particulate Concentration Grains per Actual 0.0027 0.0021 0.0024 0.0024

 Cubic Foot

Particulate Emission Rate Pounds per Hour 48.1 36.2 43.1 42.5

Particulate Emission Rate Pounds per Million 0.009 0.007 0.008 0.008

Allowable Btu (O2 F Factor) 0.3 0.3 0.3 0.3

Heat Input (O2 F Factor) Million Btu per Hour 5,479 5,286 5,653 5,472

Isokinetic Rate Percent 99.1 98.7 99.1 99.0

TABLE I. PARTICULATE EMISSIONS TEST RESULTS

GULF POWER COMPANY

PLANT CRIST - UNIT 7

SOOT BLOWING OPERATIONS
ATTACHMENT 77 - Crist Report 77 Test Results

2009 SO2 Emissions Test

Crist Unit 7

Run Unit

Number Load FUEL FLOW LBS ULTIMATE ANALYSIS BTU/LBMMBTU/HR

1 491 453180 11457 5192

2 493 464560 11457 5322

3 494 482040 11457 5523

1.311 AVERAGE= 5346

Time Time RM-6C (SO2(

Started Stopped lbs/mmBtu

4/22/09 9:30 4/22/09 10:30 1.313

4/22/09 6:52 4/22/09 7:52 1.309

4/22/09 8:11 4/22/09 9:11 1.311
ATTACHMENT 78 - Crist Report 78 Test Results

Unit 6 Multi-Method Mercury Speciation Testing (08/24/05 - 08/28/05)

Total Hg [Hg(T)] = Elemental Hg [Hg(0)] + Oxidized Hg [Hg(2+)] + Particle-bound Hg [Hg(P)] 

Vapor-phase total Hg [Hg(VT)] = Elemental Hg [Hg(0)] + Oxidized Hg [Hg(2+)]
ATTACHMENT 79 - Crist Report 79 Test Results

Units 6 & 7 EPA/EPRI/DOE Crist Blimp Study (02/18/08 - 02/29/08)

Unit 6

Date Sample Type Duct 

Temp., °F 

Moisture, 

% 

Dust 

Loading, 

grains/dscf 

Dust 

Loading, 

g/dscm 

O2, % CO2,% 

2/18/08 OH Method 334 8.8 0.0004 0.0008 8.5 11

2/18/08 OH Method 334 8.9 0.0001 0.0001 8.5 11

2/20/08 OH Method 325 8.8 0.0023 0.0052 8 11.5

2/20/08 OH Method 324 8.8 0.0018 0.0041 8 11.5

2/21/08 OH Method 333 9.4 0.0007 0.0017 8.4 11.2

2/21/08 OH Method 334 9.1 0.0007 0.0016 8.4 11.2

Average 332 8.9 0.001 0.0023 8.3 11.3

Note: Assuming an inlet dust loading of 1.5 gr/dscf the collection effiency is 99.93%

Date Moisture, % HgPart Hg0 Hg2+ HgTot HgPart Hg0 Hg2+ HgTot Hg0, % RD, % 

2/18/08 8.9 0.008 0.68 0.69 1.38 0.007 0.62 0.63 1.25 49.4 4.11

2/18/08 8.9 0.001 0.68 0.82 1.49 0.001 0.62 0.74 1.36 45.3

2/20/08 8.8 0.01 0.49 1.16 1.66 0.009 0.45 1.06 1.5 29.53 20.38

2/20/08 8.8 0.008 0.57 0.52 1.1 0.007 0.52 0.48 0.99 51.74

2/21/08 9.4 0.002 1 0.72 1.72 0.002 0.91 0.65 1.56 58.33 10.17

2/21/08 9.4 0.001 0.87 0.53 1.4 0.001 0.79 0.48 1.27 62.16

2/21/08 9.5 0.006 0.7 0.53 1.24 0.005 0.63 0.48 1.11 56.45 5.04

2/21/08 9.4 0.009 0.75 0.61 1.37 0.008 0.68 0.55 1.23 55.13

*All mercury data presented at actual oxygen concentrations.

Date Moisture % Spike, ng HgTot (dry), 

μg/Nm3 

HgTot (wet), 

μg/Nm3 

HgTot (dry), 

μg/Nm3 

HgTot (wet), 

μg/Nm3 

RD , % Spike 

Recovery% 

2/18/08 8.8 200 3.67 3.35 0.34 0.31 21.34

2/18/08 8.8 0 0.52 0.48 0.52 0.48 94.49

2/20/08 8.8 50 0.97 0.89 0.62 0.57 0.21

2/20/08 8.8 0 0.62 0.56 0.62 0.56 100.73

2/21/07 9.4 50 1.41 1.28 1.04 0.94 0.23

2/21/07 9.4 0 1.04 0.94 1.04 0.94 101.28

2/21/07 9.4 50 1.37 1.24 0.99 0.9 4.02

2/21/07 9.4 0 0.91 0.83 0.91 0.83 119.93

Table 6. Particle Loading at the Outlet of the ESP for Unit 6

Table 7. OH Mercury Results for Unit 6

Table 8. Carbon Trap Mercury Results for Unit 6

Note: there was a contamination issue with the solutions and glassware used for the OH method. Although, the contamination was relatively small at the very low Hg concentrations, ~1.0 

μg/Nm3 on a dry basis μg/Nm3 on a wet basis 

With Spike Spike Subtracted 
ATTACHMENT 79 - Crist Report 79 Test Results

Table 9. Mercury Method Comparison, Unit 6

Date 

OH Method, 

μg/Nm3 

Carbon 

Traps, 

μg/Nm3 

2/18/08 1.25 0.31

2/18/08 1.36 0.48

2/20/08 1.5 0.57

2/20/08 0.99 0.56

2/21/07 1.56 0.94

2/21/07 1.27 0.94

2/21/07 1.11 0.9

2/21/07 1.23 0.83

Unit 7

Date Sample Type Duct Temp 

F 

Moisture 

% 

Dust 

Loading 

grains/dscf 

Dust 

Loading 

g/dscm 

O2, % CO2,% 

2/23/08 Method 29 311 8.1 0.0023 0.0052 8.1 11.4

2/24/08 Method 29 319 8.5 0.0037 0.0086 8 11.5

2/25/08 Method 29 319 9 0.0026 0.006 8.2 11.3

2/27/08 Method 29 306 6.9 0.0018 0.0041 8.4 11.2

2/28/08 Method 29 316 7.1 0.0016 0.0036 7.9 11.6

2/23/08 OH Method 317 7.6 0.0027 0.0062 8.1 11.4

2/23/08 OH Method 317 8.1 0.003 0.0069 8.1 11.4

2/24/08 OH Method 319 7 0.003 0.0068 8 11.5

2/24/08 OH Method 319 8 0.0028 0.0064 8 11.5

2/25/08 OH Method 319 7.9 0.0019 0.0044 8.2 11.3

2/25/08 OH Method 319 8.4 0.0021 0.0048 8.2 11.3

2/27/08 OH Method 304 7.4 0.0006 0.0013 8.4 11.2

2/27/08 OH Method 305 7.5 0.0009 0.0021 8.4 11.2

2/28/08 OH Method 315 7 0.0006 0.0014 7.9 11.6

2/28/08 OH Method 316 6.3 0.0006 0.0014 7.9 11.6

2/29/08 OH Method 315 8 0.0009 0.002 7.9 11.6

2/29/08 OH Method 315 7.9 0.0009 0.002 7.9 11.6

Average 315 7.7 0.0019 0.0043 8.1 11.4

Note: Assuming an inlet dust loading of 1.5 gr/dscf the collection effiency is 99.87% 

Date Moisture, % HgPart Hg0 Hg2+ HgTot HgPart Hg0 Hg2+ HgTot Hg0, % RD, % 

2/23/08 7.6 0 1.34 6.6 7.94 0 1.24 6.1 7.34 16.93 4.1

2/23/08 8.1 0 1.25 7.37 8.62 0 1.15 6.77 7.92 14.56

2/24/08 8 0 0.48 6.21 6.69 0 0.45 5.77 6.22 7.22 1.97

2/24/08 7 0 0.55 5.88 6.43 0 0.5 5.41 5.91 8.52

2/25/08 7.9 0 0.41 6.14 6.56 0 0.38 5.66 6.04 6.31 0.09

2/25/08 8.4 0 0.4 6.17 6.57 0 0.37 5.65 6.01 6.09

2/27/08 7.4 0.001 0.84 5.89 6.73 0.001 0.78 5.46 6.24 12.49 1.3

2/27/08 7.5 0.001 0.59 5.97 6.56 0.001 0.54 5.53 6.07 8.93

2/28/08 7 0.001 1.21 5.99 7.2 0.001 1.13 5.57 6.69 16.85 12.41

2/28/08 6.3 0.001 1.05 4.56 5.61 0.001 0.98 4.28 5.26 18.65

3/1/08 8 0.001 0.2 6.05 6.25 0.001 0.18 5.56 5.75 3.2 0.49

3/1/08 7.9 0.008 0.59 5.59 6.19 0.008 0.55 5.14 5.69 9.58

Table 11. Particle Loading at the Outlet of the ESP for Unit 7

μg/Nm3 on a dry basis μg/Nm3 on a wet basis 

Table 12. OH Mercury Results for Unit 7
ATTACHMENT 79 - Crist Report 79 Test Results

Date Moisture % Spike, ng HgTot (dry), 

μg/Nm3 

HgTot (wet), 

μg/Nm3 

HgTot (dry), 

μg/Nm3 

HgTot (wet), 

μg/Nm3 

RD , % Spike 

Recovery% 

2/23/08 7.6 200 13.98 12.92 7.01 6.48 4.5

2/23/08 8.1 0 6.4 5.89 6.4 5.89 108.7

2/24/08 8 200 13.39 12.32 6.4 5.89 0.3

2/24/08 7 0 6.36 5.92 6.36 5.92 100.5

2/25/08 7.9 200 12.94 11.92 6.43 5.92 3.3

2/25/08 8.4 0 6.01 5.51 6.01 5.51 106.4

2/27/08 7.4 200 13.71 12.69 7.26 6.72 7.5

2/27/08 7.5 0 6.25 5.79 6.25 5.79 115.6

2/28/08 7 0 6.22 5.78 6.22 5.78 2.2

2/28/08 6.3 0 6.5 6.09 6.5 6.09 – 

3/1/08 7 0 6.99 6.5 6.99 6.5 4.6

3/1/08 7 0 6.38 5.93 6.38 5.93 – 

Date 

OH Method, 

μg/Nm3 

 Carbon 

Traps, 

μg/Nm3 

EPA 

Method 

29,μg/Nm3 

2/23/08 7.34 6.48 6.66

2/23/08 7.92 5.89

2/24/08 6.22 5.89 8.34

2/24/08 5.91 5.92

2/25/08 6.04 5.92 5.95

2/25/08 6.01 5.51

2/27/08 6.24 6.72 4.78

2/27/08 6.07 5.79

2/28/08 6.69 5.78 4.73

2/28/08 5.26 6.09

3/1/08 5.75 6.5 –– 

3/1/08 5.69 5.93

 Date 

Hg in Flue Gas 

based on Coal, 

μg/Nm3 

 Hg in 

Flue Gas, 

μg/Nm3 

 Removal, 

% 

Speciation

, 

Percentag

e Hg0 

inFlue Gas 

2/23/08 8.85 6.86 22.5 15.7

2/24/08 10.42 6.46 38 7.9

2/25/08 10.52 5.89 44 6.2

2/26/08 11.11 5.92 46.7 10.7

2/28/08 11.94 5.71 52.2 17.8

3/1/08 10.57 5.97 43.5 6.4

With Spike Spike Subtracted 

Table 13. Carbon Trap Mercury Results for Unit 7

Table 14. Mercury Methods Comparison, Unit 7

Table 15. Summary of Mercury Measurements for Unit 7
ATTACHMENT 79 - Crist Report 79 Test Results

Element Part Vapor Total Part Vapor Total Part Vapor Total Part Vapor Total Part Vapor Total 

Antimony 0.762 <0.3 0.762 0.828 <0.03 0.828 0.646 <0.03 0.646 0.632 <0.03 0.632 0.526 <0.03 0.526

Arsenic 6.36 1.8 8.14 6.46 7.5 13.98 5.5 <0.1 5.5 4.61 <0.1 4.61 2.31 <0.1 2.31

Bismuth 0.031 <0.03 0.031 0.039 <0.03 0.039 0.031 <0.03 0.031 0.029 <0.03 0.029 0.025 <0.03 0.025

Cadmium 0.111 <0.03 0.111 0.144 <0.03 0.144 0.109 <0.03 0.109 0.097 <0.03 0.097 0.082 <0.03 0.082

Calcium 208 0.05 208 253 0.02 253 198 0.05 198 199 0.06 199 160 0.07 160

Gallium 5.08 <0.3 5.08 6.19 <0.3 6.19 5.1 <0.3 5.1 5.53 <0.3 5.53 4.94 <0.3 4.94

Iron 496 <0.013 496 610 <0.013 610 484 <0.013 484 405 <0.013 405 286 <0.013 286

Lead 6.97 1.91 8.88 6.08 1.11 7.19 6.59 1.29 7.87 3.68 1.44 5.12 1.67 1.62 3.29

Magnesium 86.2 <0.008 86.2 108.7 <0.008 108.7 86.2 <0.008 86.2 86.3 <0.009 86.3 75.8 <0.009 75.8

Manganese 2.5 <1.3 2.5 3.4 <1.3 3.4 2.4 <1.3 2.4 2.2 <1.3 2.2 2.2 <1.3 2.2

Mercury 0.001 6.66 6.66 0.001 8.34 8.34 0.001 5.95 5.95 0.001 4.78 4.78 0.008 4.73 4.73

Nickel 2.58 1.25 3.83 2.58 1.38 3.96 2.31 3.7 6 1.7 1.33 3.03 1.2 1.17 2.37

Phosphorus 19 <0.08 19 22 <0.08 22 16 <0.08 16 13 <0.09 13 11 <0.09 11

Potassium 90 0.25 90 146 0.18 146 123 0.17 124 87 0.16 87 64 0.21 64

Selenium 3.24 95 98.24 3.28 134 137.28 2.12 84 86.12 4.37 50 54.37 6.89 38 44.89

Vanadium 4.71 3 7.71 6 2.42 8.42 4.98 2.5 7.48 4.17 1.75 5.91 3.48 1.14 4.62

Zinc 18.3 8.2 26.5 17.2 5.8 23 16.5 6.2 22.7 13.7 5.6 19.3 11.3 4.4 15.7

*The total values reported assume the less than values are zero.

2-23-08 

μg/Nm3 on a wet basis μg/Nm3 on a wet basis 

Table 16. Trace Element Results for Unit 7 (EPA Method 29)*

μg/Nm3 on a wet basis 

2-24-08 2-25-08 2-27-08 2-28-08 

μg/Nm3 on a wet basis μg/Nm3 on a wet basis