March 4,2013 

Carey Willoughby 

Monitoring and Analysis Division 

Source Test Engineering 

South Coast Air Quality Management District 

21865 Copley Drive 

Diamond Bar, CA 91765-4182 

Subject: Initial Source Test Report for Unit 2 

CPV Sentinel, LLC (CEC Docket No. 07-AFC-3) 

SCAQMD Title V (A/N 472137, Facility ID No. 152707) 

Dear Mr. Willoughby: 

. sierra 

research 

1801 J Street 

Sacramento CA 95811 

Tel: (916) 444-6666 

Fax: (916) 444-8373 

Ann Arbor MI 

Tel: (734) 761-6666 

Fax: (734) 761-6755 

On behalf of CPV Sentinel, LLC, I am submitting the enclosed initial source test report 

for Unit 2 at the CPV Sentinel Energy Project. Testing was conducted in accordance 

with Condition of Certification AQ-7 and Section H, Condition D29.3 of facilities Title V 

Permit. 

Should you have any questions or require additional information related to this submittal, 

please contact me at (916) 444-6666. 

Sincerely, 

Tom Andrews 

Senior Engineer 

CC: Roy Olivares, SCAQMD 

Craig Hoffman, California Energy Commission 

EPA Region 9 (r9.aeo@epa.gov) 

Charles Aldred, EPA Region 9 

Mark McDaniels, CPV Sentinel, LLC 
SOURCE TEST REPORT FOR INITIAL COMPLIANCE 

TESTING AT CPV SENTINEL ENERGY PROJECT UNIT 2 

PREPARED FOR: 

GEMMA POWER SYSTEMS CALIFORNIA, INC. 

2461 MAIN STREET 

GLASTONBURY, CONNECTICUT 06033 

FOR SUBMITTAL TO: 

SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 COPLEY DRIVE 

DIAMOND BAR, CALIFORNIA 91765-4178 

PREPARED BY: 

DELTA AIR QUALITY SERVICES, INC. 

1845 N. CASE ST. 

ORANGE, CALIFORNIA 92865 

714-279-6777 

ARLENE BELL / ROBERT A. FINKEN 

FEBRUARY 28,2013 

REPORT NUMBER: R0410673 

Dellaf). Air Quality Services, Incorporated 
CONFIDENTIALITY STATEMENT 

This information contained in this communication is intended exclusively 

for the individual or entity to which it is addressed. This communication may 

contain information that is proprietary, privileged or confidential or otherwise 

legally exempt from disclosure. If you are not the named addressee, you are not 

authorized to read, print, retain, copy, or disseminate this message or any part of 

it. 

R0410673 ii 
REPORT REVIEW AND CERTIFICATION 

I certify that all work performed in the preparation and production of this report 

was performed by me or under my supervision and that all data presented is authentic. 

_-------I.a.LL!l'<L\,'---'-"'~=--=---E--J,v_A_9_ Date: 

I 

Arlene Bell 

Vice President, Analytical Services 

I certify that I have also reviewed this report, both in form and content, and that all 

data, calculations, and presentations are authentic, accurate, and complete. 

R0410673 

Robert A. Finken 

President 

iii 
CONTENTS 

SECTION PAGE 

1.0 INTRODUCTION AND SUMMARy ................... .... . • .. .... ......... 1 

2.0 UN IT DESCRIPTION AND TEST CONDITIONS . .... ..... .............................. .......... 3 

2.1 UNIT DESCRIPTION ................................. .... . ...... ............ .... . 3 

2.2 TEST CONDITIONS... ... ........ ... ........ ... ..................... ... ... ...... ..... 5 

2.3 SAMPLE LOCATION .. .................... ..................... ....... ....... ..... ...... ........ .... ..... 6 

3.0 TEST DESCRIPTION .. .... .. ...... .... ..... .. ..... ...... ..... .... ..... ..... ................. .... .. ....... ...... .... 9 

3.1 O2, CO2, NOx AND CO ....... ... .... ................ ...................... ......... ..... .... ........ 10 

3.2 NH3 BY SCAQMD METHOD 207.1 .. .. ... ...... .. ..... .. ....... . .. ...... ... 11 

3.3 SOx BY SCAQMD METHOD 307.91 ................................ . . .... 11 

3.4 ROG BY MODIFIED SCAQMD METHOD 25.3 .. ........ ..... ..... ... . ... .... 11 

3.5 PM BY SCAQMD METHOD 5.1 ... ...... ..... .. .... .... .. ... .. . .. .. .. 14 

4.0 RESULTS .... ..... .. .. .. ... .. .... ..... .. ..... ................... ....... . ... . ... 16 

5.0 DISCUSSION AND TEST CRITIQUE .. ..... . . ..... .......... ........... 24 

APPENDICES 

A QUALITY ASSURANCE .... ...... . .. ..... ............................. . .. ............ .... A-1 

A.1 Quality Assurance Program Summary ... ............................ ..... ...... ............ A-2 

A.2 SCAQMD and CARB Certifications ............ ......... ... ....... .................. .. ....... A-7 

A.3 Equipment Calibration and Calibration Gas Certificates ..... ... . ... .. . .... A-8 

A.4 Delta CEM System Description and SCAQMD Method 100.1 

Calibration and Test Sequence . ... ................... .. . .... A-9 

B PROCESS DATA .... .. .. ... ..... . .......... ...... . .. .. .. ..... . .. ... ............ B-1 

B.1 Process and CEMS Data. .... .... . ........ .............. .. . .. . B-2 

B.1.1 Sentinel Unit 2 Stratification Test ........ .... . ... ... . ............ .. B-3 

B.1.2 Sentinel Unit 2 Ammonia, ROG, and NOx/CO Testing ..... B-4 

B.1.3 Sentinel Unit 2 PM Testing .... ..... .. ... ... ... ..... . .... ......... .. .. .. . ..... B-5 

B.2 Fuel Analysis Data .. ... ...... .. .. ......... .. ............ .............. .. ...... ....... ...... ..... ..... B-6 

C TEST DATA. ... ...... ... ... .. ........ ........ ....... ...... ..... ................... ..... ..... .. ...... ..... ... C-1 

C.1 Stratification and Preliminary Flow Rate Tests .. ....... ....... ...... .. .... ..... .. .... ...... C-2 

C.2 CEM Data... . ..... ...... .. ... ... ......... . ........................... .... .. .. ...... ..... . ..... .. C-3 

C.2.1 CEM Quality Assurance Measurements ............. .......... ... .. ... .... . .. C-4 

C.2.2 NOx and CO Compliance ..... .... ....... .... ... .. ... .... . ............ ... C-5 

C.2.3 One Minute Data Logger Data. .. ...... ... ... .... ... .... . .. C-6 

C.3 Ammonia Data by SCAQMD Method 207.1.. ...... ........ .... . ...... .... .... ..... C-7 

C.4 SOx by SCAQMD Method 307.91 ........ .... ... ... ... .... .... . ..... C-8 

C.5 ROG by Modified SCAQMD Method 25.3...... . ... C-9 

C.6 PM by SCAQMD Method 5.1................ ........ ... . ... .. ... .. .. ........... . . .... C-10 

R0410673 iv 
o 

E 

F 

G 

H 

GENERAL EMISSIONS CALCULATIONS ........... ........... .. ............................... 0-1 

CHAIN OF CUSTODY ................................................. .......................................... E-1 

INSTRUMENT STRIP CHARTS ........................................ ........... .. ........ ........... F-1 

FACILITY PERMIT TO OPERATE CONDITION D29.1 ............. . ....... .......... ..... G-1 

CORRESPONDENCE AND TEST PLAN .... ... .......... .... ...... .... . .. ......... ....... ... . H-1 

R0410673 v 
1.0 INTRODUCTION AND SUMMARY 

Delta Air Quality Services, Inc. has been contracted by Gemma Power Systems 

California, Inc. (GEMMA) to perform the initial Permit to Operate Compliance Testing at 

the CPV Sentinel Energy Project Units 1, 2, 3, 4, 5, 6, 7, and 8. Condition D29.1 of the 

Permit to Operate requires source tests within 180 days of initial startup. 

This document is the test report for the initial compliance for CPV Sentinel Unit 2. 

Tests were performed at three load conditions to determine oxides of nitrogen 

(NOx), carbon monoxide (CO), oxides of sulfur (SOx), reactive organic gases (ROG), 

particulate matter (PM), and ammonia (NH3) emissions. 

Bob Finken was the Senior Program Manager for Delta and can be reached at 

(714) 279-6777. No conflict of interest, as defined in SCAQMD Rule 304, exists between 

Gemma or CPV Sentinel Energy Project and Delta. 

Testing was conducted on January 30-31 and February 1, 2013. The Delta test 

crew consisted of Ali Aleshaiker, Shannon Scrugham, and Justin Miller. 

Table 1-1 contains a summary of the test results and applicable limits. This table 

also compares the results at three load conditions, 50%, 75%, and 100%, that were 

tested. All test results showed the unit to meet the permit limits. 

Section 2.0 of this document provides a description of the facility and sample 

locations. A description of the sampling strategy and test methods is provided in Section 

3.0. Section 4.0 contains detailed test results. Section 5 contains a discussion and test 

critique. The appendices contain all test and laboratory data, calculations , and quality 

assurance data. 

R0410673 1 
TABLE 1·1 

CPV SENTINEL ENERGY PROJECT 

UNIT 2 

STACK TEST RESULTS SUMMARY 

Parameter Units 100% 75% 50% Limit Rule 

ppm@ 15%0, 2.37 2.22 202 2.5 1703(a)(2) 

NO, ppm @ 15% 0, 2.37 2.22 2.02 15 40 CFR 60 

Ib/MMscf 9.38 9.01 8.48 12.2611 ) 2012 

CO ppm @ 15% 0, 1.89 0.52 0.25 4 1703(a)(2) 

NH, ppm@ 15% 0, 1.51 0.98 0.73 5 1303(a)(1 ) 

gr/dscf @ 3% 0, 0.0005 0.0004 0.0005 0.01 475 

Particulate gr/dscl @ 12% CO, 0.0007 0.0005 0.0005 0.1 409 

Ib/hr 0.75 0.49 0.42 11 475 

PM,0/PM'5 Ib/MMscf 0.89 0.71 0.78 5.71 1') 

so,l') Ib/MM8tu 0.0003 0.06 40 CFR 60 

gr H,S/1 00 sci 0.013 0.2514) SCAQMD Permit 

Condition 861 .1 

ROGs ppm @ 15% 0, 0.75 0.55 0.68 2.0 1303(a)(1) 

(1) The 12.261b/MMscl is a RECLAIM emission factor, not a limit. 

(2) This is stated in the permit as an emission factor. 

(3) SO, results calculated based on 100% load condition. 

(4) 0.25 gr H,S/1 00 sci sulfur content limit is based on annual average of monthly sample results. 

R0410673 2 De/lab. .. ~ ...................... 
2.0 UNIT DESCRIPTION AND TEST CONDITIONS 

2.1 UNIT DESCRIPTION 

CPV Sentinel Energy Project is located at 62575 Powerline Road, Desert Hot 

Springs, California 92240. The facility consists of eight (8) identical generating units. 

The CPV Sentinel Energy Project consists of eight (8) LMS100PA combustion 

turbines in simple cycle operation. The units are natural gas fired with a rated heat input 

of 891 .7 MMBtu per hour at 72 degrees Fahrenheit. Each LMS100PA employs water 

injection and is equipped with a CO catalyst and Selective Catalytic Reduction (SCR) 

system for NO, control. 

The LMS100PA is a General Electric (GE) combustion turbine with an intercooler 

located between the low pressure compressor (LPC) and high pressure compressor 

(HPC). Off engine combustion air to closed loop water intercooling is used for increased 

gas turbine thermal efficiency. Heat removed from the off-engine intercooler is circulated 

through a closed loop cooling system. Heat is rejected from the closed loop cooling 

system to an open loop cooling system via a shell and tube heat exchanger. The open 

loop system rejects heat via a mechanical draft counterflow cooling tower. The cooling 

tower is provided with drift elimination to comply with air emissions limits. 

Figure 2-1 presents a block diagram of the units. Figure 2-2 shows a general 

arrangement of the major components. 

R0410673 3 
FIGURE 2-1 

SIMPLIFIED PROCESS BLOCK DIAGRAM 

CPV SENTINEL ENERGY PROJECT COMBUSTION TURBINES 

Simplified Process Flow Diagram 

Air 

Water 

Air 

Cooling Tower 

Closed Loop 

Cooling 

LMS100PA 

Natural Gas Fuel 

Water 

Demineralized 

R0410673 

Air 

Water 

Heat 

Exhaust to Atm. 

Exhaust CO Catalyst SCR I--

Ammonia 

19% Aqueous 

4 
FIGURE 2-2 

GENERAL ARRANGEMENT OF MAJOR COMPONENTS 

~ ~ ~ ~ ~J 

~:~; I I,. ~ 

-_ ... . _-- _ .. _._ ... ' .. _-_ ... . .. . .. . .. . . .. . -... .. -... 

~""~,,,,,< ~ ."'0' t .... r " ..... ,( 

! ' , 

i /-· k-........ ~ , 

, 

, , 

-L~~ , 

, 

c ··- , , 

>.( , I .... c...o:;a:_k. , , ,--l- ll=:::::::::. ~ , , , , , 

~~ ~ 

, , 

'_Iv , , , , 

! 

, , j ~~ ,," ~ i , -~ : ;;;- I~ ;;E " "_",, ,_ .. ~<lU"" """". 

:$ .7 

n ~ 

I~ 'I() .'- " B ! [I / r .,.; . .... , 

I \ = 2>J . . , b , \ [j I , I [; 

. co . 

~ .::TI , "V ""..3 

I litH : ~}~' ~~ 

I / [~~7:: .. ~ [' t''' 1'' ''''' ~ (I.I ....--" ~ 

I rut tvt:·( 

""""""".,: lUO 

~I -1 - - ~ 

, ' :;.,0 

~ 

I d I, ~ .... r,>l<."', ••• " 

CT;; ''''''''.' 

, I- , -- U : U \""Gl: .... -<'.J.~ , ~ .• 

• 0' ).1 

2.2 TEST CONDITIONS 

The permit requires that the tests will be performed at three operating conditions; 

1) maximum, 2) average, and 3) minimum load. Full load is nominally 100 megawatts 

and minimum load is approximately 50 megawatts. Since these will be the initial tests for 

the units and no long term average will have been established, average conditions will be 

approximated at 75% of capacity or approximately 75 megawatts. 

R041 0673 Dellab. 5 .. -...... 
Unit operating data was collected during the tests by the facility from the CEMS 

DAS. Table 2-1 below presents the average operating condition for each parameter. 

TABLE 2-1 

AVERAGE OPERATING CONDITIONS 

Parameter 50% Load 75% Load 100% Load 

Fuel Flow Rate, hscfh 5,373 6,923 8,319 

Turbine Generating Output (MW) 55 80 101 

Ammonia Flow, Ib/hr 106.4 110.0 109.9 

Exhaust Temperature, of 796 785 781 

Exhaust Flow Rates, kscfh 15,627 18,349 20,378 

Notes: Data from facility DAS except exhaust gas temperature where PM test data was used. 

Data collected during PM test intervals at each condition. 

Process data obtained during testing is contained in Appendix B. 

2,3 SAMPLE LOCATION 

There are four 4" test ports located at 90 degrees apart around the circumference 

of the 13'6" diameter stacks. The ports are located 323" downstream (2.0 diameters) of 

the nearest flow disturbance (duct breeching) 84' upstream (0.5 diameters) of the 

nearest flow disturbance (silencers). The sampling location meets the minimum 

requirements of SCAQMD Method 2.1; at least 2 diameters downstream and at least 0.5 

diameters upstream of the nearest flow disturbances. Figure 2-3 presents the details of 

the sample location. 

R0410673 6 
Stack Exit 1080.0 in. 

Silencer Bottom 925.9 in. 

Ports 841.6 in. 

Platform 789 .6 in. 

Base of Stack 518.5 in . 

Grade 0.0 in . 

FIGURE 2-3 

SAMPLE LOCATION DETAILS 

Inside Diameter, in. 

-- 162 --

T 

84 Distance A, inches, 0.5 Diameters 

! Sample ports 

T 

323 Distance B, inches, 2.0 Diameters 

.._--=E;:;:xh.:;:aust Flow 

Elevation View 

90 ft 

66 ft. 

o ft 

Prior to performing the tests, gaseous stratification was investigated with a 12 

point traverse as described in 40 CFR 75, and the presence of cyclonic flow was checked 

using the techniques described in SCAQMD Method 2. 

The results of the yaw angle and stratification checks indicate that the angle 

criteria was met. The average angle was 2.80 which meets the SCAQMD criteria of 10 

degrees or less. 

The stratification criteria was not met. Results of the stratification checks are 

presented in Table 2-2. 12-point traverses were used for ammonia, NOx, and CO 

compliance tests. 

R0410673 7 DeltatJ. "' ''''''''''''''''''"'-
TABLE 2-2 

12-POINT STRATIFICATION CHECK RESULTS 

GEMMA POWER SYSTEMS 

CPV SENTINEL UNIT 2 

0, CO, NO, CO 

Port Point % % ppm ppm 

East 3 13.52 4.24 1.59 0.09 

East 2 13.53 4.24 1.58 0.17 

East 1 13.56 4.23 1.64 0.20 

South 3 13.48 4.29 1.78 0.16 

South 2 13.48 4.29 1.81 0.23 

South 1 13.43 4.32 1.87 2.40 

West 3 13.07 4.54 2.27 1.94 

West 2 1308 4.53 2.35 1.91 

West 1 13.08 4.54 2.27 1.69 

North 3 1308 4.54 2.34 1.12 

North 2 13.08 4.55 2.40 0.60 

North 1 1307 4.55 2.53 0.57 

Average 13.3 4.4 2.0 0.9 

Maximum 13.6 4.6 2.5 2.4 

Minimum 13.1 4.2 1.6 0.1 

Maximum Difference from Average 0.3 0.2 0.5 1.5 

Max Difference (% of average) 2.0% 3.9% 24.2% 159.6% 

Criteria: 

If < 10%, use single point. 

Action Taken: 

12-point traverse used for RATA runs 

Runs in conjunction with NH3 test, use 12-point traverse 

Table 2-3 illustrates the location of sample traverse pOints for each type of test. 

TABLE 2-3 

SAMPLE POINT LAYOUT 

PM (24 pts.) Cyclonic Flow Check (16 pts .) StraUNH3, NO" and CO 

Compliance (12 Pts.) 

Sample % of in. % of in. % of in. 

Point Diameter from Wall Diameter from Wall Diameter from Wall 

2.1 3,4 3.2 5.2 4.4 7.1 

2 6.7 10.9 10.5 17.0 14.6 23.7 

3 11 .8 19.1 19,4 31,4 29.6 48.0 

4 17.7 28 .7 32.3 52.3 70,4 114.0 

5 25 40.5 67.7 109.7 85,4 138.3 

6 35.6 57.7 80.6 13Q.6 

7 64,4 104.3 89.5 145.0 

8 75 121.5 

9 82.3 133.3 

10 86,4 140.0 

11 93.3 151.1 

12 97.9 

R0410673 8 Delta!'!. 

.. """'~ ......... -.... 
3.0 TEST DESCRIPTION 

Table 3-1 summarizes the test methods and techniques that were used as the 

reference methods. The test matrix has been developed to meet the requirements of 

Section 29.1 of the facility Permit (Application Number 472137) dated April 15, 2011 . 

The test matrix indicates the number of runs that were performed for each 

parameter and each condition . 

The permitted emission limits are summarized in Table 3-2. The following 

sections describe each method in further detail. Flue gas oxygen and carbon dioxide 

concentration were measured in conjunction with all tests using SCAQMD Method 100.1. 

The flue gas flow rate was measured in conjunction with each ammonia and particulate 

test. This measured flue gas flow rate was used for all emission rate calculations of NOx, 

CO, NH3, ROGs and SOx. 

Parameter 

NOx 

0 2/C02 

CO 

NH3 

S02 

PM 

ROG 

Method 

SCAQMD 100.1 

SCAQMD 100.1 

SCAQMD 100.1 

SCAQMD 207.1 

TABLE 3-1 

TEST MATRIX 

SENTINEL UNIT 2 

50% Load 75% Load 

2 runs' 2 runs'" 

With each run 

2 runs' 2 runs'" 

2 runs 2 runs 

100% Load 

2 runs' 

2 runs' 

2 runs 

SCAQMD 307.91 Fuel Sample, 2 Samples 

SCAQMD 5.1 3 runs· 1 run run 

Modified SCAQMD 25.3 1 pair 1 pair 1 pair 

Test Duration 

60 minutes 

60 minutes 

60 minutes 

N/A 

240 minutes 

- 60 minutes(1 ) 

1) ROG tests were nominally 60 minutes. Flow controllers will be setup for 60 minutes. The test was 

performed until the canister vacuum reaches approximately 10 "Hg. Actual test time may be less than or 

more than 60 minutes per sample . 

• Additional runs performed compared to test plan. 

R0410673 9 
TABLE 3-2 

CPV SENTINEL ENERGY PROJECT 

PERMITTED EMISSION LIMITS 

Parameter Units 

ppm@ 15%02 

NO, ppm@ 15% O2 

Ib/MMscf 

CO ppm @ 15% O2 

NH3 ppm@ 15% O2 

gr/dscf @ 3% O2 

Particulate grldscf @ 12% CO2 

Ib/hr 

PMlO/PM25 Ib/MMscf 

SO, Ib/MM8tu 

gr H2S/1 00 scf 

ROGs ppm @ 15% O2 

(1) The 12.261b/MMscf is a RECLAIM emission faclor, not a limit. 

(2) This is staled in the permit as an emission faclor. 

Limit 

2.5 

15 

12.26(1) 

4 

5 

0.01 

0.1 

11 

5.71 (2) 

0.06 

0.25(3) 

2.0 

Rule 

1703(a)(2) 

40 CFR 60 

2012 

1703(a)(2) 

1303(a)(1 ) 

475 

409 

475 

40 CFR 60 

SCAQMD Permit 

Condition 861.1 

1303(a)(1 ) 

(3) 0.25 gr H2S/100 scf sulfur can lent limit is based on annual average of monthly sample results. 

3.1 O2• CO2• NOx AND CO 

O2, CO2, NO, and CO concentrations were measured using SCAQMD Method 

100.1. These measurements were made with one of Delta's mobile emission 

measurement laboratories. The system consists of a stainless steel or glass probe, 

heated Teflon line, moisture removal system, sample pump, sample filter, unheated 

Teflon line, and individual component analyzers. The measured concentrations are 

averaged over each sampling period, then corrected for system bias and analyzer drift. 

All quality assurance procedures required by SCAQMD Method 100.1 were 

performed including pre- and post-test Calibration Error, Sample System Bias and 

Analyzer Drift. 

The sampling was performed using a 12-point traverse at each test condition. At 

the 75% load condition, the compliance test was performed concurrently with the Relative 

Accuracy Test Audit (RATA). In this case, data from the RATA was used to demonstrate 

compliance with the NO, and CO emission limits. 

R0410673 10 "'_ Dellai'!. ..... w._ .... 
NO, concentrations were measured on a 0-5 ppm range. CO concentrations 

were measured on a 0-10 ppm range. CO2 concentrations were measured on a 0-10% 

range. O2 concentrations were measured on a 0-20% range. 

The measured concentrations are averaged over each sampling period , then 

corrected for system bias and analyzer drift. The drift and bias corrected result were 

then used to calculate emissions in units required by the permit including ppm , ppm 

corrected to 15% O2, pounds per hour, and pounds per million standard cubic feet of 

natural gas. 

3.2 NH3 BY SCAQMD METHOD 207.1 

Duplicate flue gas samples were collected non-isokinetically at each test condition 

using SCAQMO Method 207.1. A 12-point traverse was performed during each NH3 slip 

test. 

The sample gas is drawn through a glass probe, Teflon sample line, two 

impingers each containing approximately 100 ml of 0.1 N H2S04 , an empty impinger, an 

impinger containing silica gel, and a dry gas meter. The optional nozzle and filter were 

not used since the units are natural gas fired. The contents of the probe, sample line 

and the first three impingers are recovered and analyzed by SCAQMO Method 207.1 for 

ammonia concentration using the Ion Selective Electrode technique. One reagent blank 

sample, one 01 water sample, and one field blank sample was analyzed. 

Ammonia slip is reported in units of ppm, corrected to 15% O2 . 

The tests were performed over a period of at least 60 minutes. 

3.3 SOx BY SCAQMD METHOD 307.91 

Oxides of sulfur were measured using SCAQMO Method 307-91 . Two fuel 

samples were collected in Tedlar bags and sent to Saybolt Laboratory for sulfur analysis 

as total reduced sulfur as H2S. 

3.4 ROG BY MODIFIED SCAQMD METHOD 25.3 

Sampling and analyses are performed using Modified SCAQMO Method 25.3 

procedures. The sample apparatus and analyses are provided by Atmospheric Analysis 

and Consulting (MC) in Ventura California. 

At each test condition, two (one paired sample, consist of 2 canisters) flue gas 

samples are extracted simultaneously from four points (one per port) in the stack through 

pre-cleaned (high temperature conditioned) stainless steel probes connected to an outof-stack flow controller, into stainless steel Summa polished canisters. The flow 

controller is set to fill the evacuated canister to a pressure of -400 mm Hg over a period 

of a period of one hour. 

R0410673 11 
Modifications to the Method 25.3 sampling procedures suggested or accepted by 

SCAQMD are: 

• Elimination of the in-stack filter 

• Elimination of the water vial portion of the 25.3 equipment 

• The final pressure in the Summa Canisters is maintained at between 400 and 

500 mm HG (10 -14 in. Hg) absolute. 

Figure 3-1 presents a schematic drawing of the sample apparatus . 

FIGURE 3-1 

MODIFIED SCAQMD METHOD 25.3 SAMPLING APPARATUS 

Filter Probe 

Flex Line 

Flow Controller 

R0410673 12 

Della/'). .'"_ ......... ,-
The samples are analyzed for NMNEOC (Non-Methane Non-Ethane Organic 

Compounds, i.e. Reactive Organic Compounds ROG) using modified SCAQMD Method 

25.3 TCA procedures. Analysis consists of a fore-flush and back-flush of a gas 

chromatography (GC) column, followed by an oxidizer, a methanizer, and a flame 

ionization detector (FlO). The GC separates the NMNEOC from other constituents of the 

sample (methane, ethane, CO2, H20, O2, N2 , etc.). The oxidizer converts the NMNEOC 

to carbon dioxide. The methanizer converts the resulting CO2 to methane. The methane 

content is detected by the FlO as ppmcarbon. 

Modifications suggested by SCAQMD to the Method 25.3 analytical procedures 

approved for MC under the lAP are: 

• Pressurization of the canisters to 900 mm Hg with Ultra High Purity (UHP) 

helium analyzed/certified to contain less than 0.05 ppmv of total hydrocarbons 

as carbon 

• Analyzing only the Summa canister fraction of the normal 25.3 sample. No 

water vial used in sampling, no water vial analysis . 

• Utilization of a larger (-2 ml) sampling loop 

• Development of a custom low level (0.1 - 5.0 ppmV propane) calibration 

curve 

• Performance of a Minimum Detection Limit (MOL) study 

• Determination of a Practical Quantitation Limit (PQl) from the MOL study 

Results are reported in parts per million by volume as carbon to 2 significant 

digits, corrected to 15% O2 using the O2 from the CEM measurements. The average of 

the results for the duplicate samples is compared to the Emission Standard for 

determination of the compliance status. 

Detailed procedures from SCAQMD concerning the application of the modified 

SCAQMD Method 25.3 to permit condition 029.1 are located in the test plan in Appendix 

H. 

R0410673 13 
3.5 PM BY SCAQMD METHOD 5.1 

Particulate matter was measured using SCAQMD Method 5.1. SCAOMD Method 

5.1 is cited as the table in Condition D29.1 lists District Method 5. District Method 5.1 

measures total particulate. This total particulate measurement could include material 

>10 microns. Use of the cyclone as in 201A prevents overstating of PM10 emissions if all 

of the PM emissions from these units are not PM1O. It was assumed for reporting 

purposes that the SCAOMD Method 5.1 total PM results will be used to determine PM10 

compliance. 

A single test was required to be performed at each of the three conditions; 100%, 

75%, and 50% load conditions. Triplicate tests were performed at the 100% load 

condition to ensure sufficient data were collected. All results are included in the average 

result. 

Flue gas is drawn through a stainless steel nozzle, glass or stainless steel probe, 

unheated Teflon line followed by four impingers. Impingers #1 and #2 contain 

approximately 100 ml of deionized water, impinger #3 is empty, and impinger #4 contains 

silica gel. A backup filter is placed between impingers #3 and #4. The sample was 

collected isokinetically (90 - 110%) using a 24-point traverse at the exhaust stack 

location. Each point was sampled for 10 minutes resulting in a 240 minute sample time 

pertest. 

Figure 3-3 presents a diagram of the sampling system. 

R041 0673 14 
FIGURE 3-3 

SCAQMD METHOD 5.1 SAMPLE SYSTEM 

Temperature 

Sensor Probe 

~ PijotTube Connecting 

Teflon Tubing Filter Temperature 

" Sensor 

: ---------impCngers ~ --- , 

Nozzle 

"..~~~~ 

/ 

S· Type Pitot Tube 

Manometer 

Orifice 

R0410673 

Temperature Water 

Sensors 

Dry Gas 

Meter 

15 

Empty Silica 

Gel 

Vacuum 

Line 

Della/'-,. """""''"''''-,-
4.0 RESULTS 

The test results are presented in the following tables: 

Table 4-1 

Table 4-2 

Table 4-3 

Table 4-4 

Table 4-5 

Table 4-6 

Table 4-7 

NO" CO, Ammonia (NH3), and ROG - 100% load 

PM results - 100% load 

NO" CO, NH3, and ROG - 75% load 

PM results - 75% load 

NO" CO, NH3 , and ROG - 50% load 

PM results - 50% load 

SO, results 

Additional test runs were performed for some parameters to ensure that sufficient 

valid data were collected. Table 3-1 contains a test matrix with this information. 

Additional data is presented in the Appendices, including all field data, laboratory 

data, and calculations. 

R0410673 16 
TABLE 4-1 

COMPLIANCE TEST RESULTS 

CPV SENTINEL ENERGY PROJECT 

SENTINEL UNIT 2 

NO .. CO, NH3, AND ROG 

100% LOAD 

JANUARY 30, 2013 

Test Number Run 1 Run 2 Average Limit 

Condition 103 MW 103 MW 

Test Date 1/30/2013 1/30/2013 

Star! Time 11 :01 13: 11 

Stop Time 12:17 15:05 

Fuel Flow, hscfh 8,438 8,434 

Stack Flow Rate, dscfm 339,745 344,040 

Stack 0, (%) 12.98 12.97 12.98 

Stack NO. (ppm) @ 15% 0, 2.49 2.25 2.37 2.5 

Stack NO. (lb/MMscf) 9.78 8.98 9.38 12.26(') 

Stack CO (ppm) @ 15% 0, 2.21 1.58 1.89 4 

Moisture Fraction (%) 0.104 0.103 

PPM NH3 (flue gas) 1.87 2.19 2.03 

PPM NH3 @ 15% 0, 1.39 1.63 1.51 5 

Ib/hr NH, 1.70 202 1.86 

Ib/MMscf fuel NH, 2.02 240 2.21 

Stack ROG(1), ppm @ 15% 0, 0.75 0.75 2.0 

1) Collected as a simultaneous pair. 

2) The 12.26 Ib/MMscf is a RECLAIM emission factor, not a limit. 

3) Higher ROG result shown of pair. RDP was 23.9%. Lower ROG result was 0.46 ppm @ 15% 0,. 

R041 0673 17 
TABLE 4-2 

COMPLIANCE TEST RESULTS 

CPV SENTINEL ENERGY PROJECT 

SENTINEL UNIT 2 

PM -100% LOAD 

JANUARY 30-31, 2013 

Test Number S-2/STK-PM-100-1 S-2/STK-PM-100-2 S-2/STK-PM-100-3 Average Limit 

Condition 103 MW 100 MW 100 MW 

Test Date 1/30/2013 1/30/2013 1/31/2013 

Start Time 9:26 13:45 8:33 

Stop Time 13:34 17:51 1239 

Fuel Flow, hscfh 8,459 8,239 8,260 

Stack Flow Rate, dscfm 366,608 352,398 368,538 

Stack 0" % 13.07 13.24 13.08 

Stack CO" % 4.42 4.34 4.42 

Moisture Fraction, % 0.103 0.096 0.103 

Particulate Emissions 

Grain Loading, gr/dscf 0.0003 0.0002 0.0002 0.0002 

Grain Loading @ 3% 0, 0.0007 0.0004 0.0005 0.0005 0.01 

Grain Loading @ 15% 0, 0.0002 0.0001 0.0002 0.0002 

Grain Loading @ 12% CO, 0.0009 0.0005 0.0006 0.0007 0.1 

Mass Emissions, Ib/hr 1.02 0.54 0.67 0.75 11 (1) 

Emission Rate, Ib/MMscf 1.21 0.66 0.82 0.89 5.71(') 

(1 ) 11 Ib/hr PM limit from SCAQMD Rule 475. 

(2) This is stated in the permit as an emission factor. 

R0410673 18 Oeltat-.. .. 0..0.>-"., ... ..,.. .... 
TABLE 4-3 

COMPLIANCE TEST RESULTS 

CPVSENTINELENERGYPROJECT 

SENTINEL UNIT 2 

NO" CO, NH3, AND ROG 

75% LOAD 

FEBRUARY 1, 2013 

Test Number Run 1 Run 2 Average Limit 

Condition 80MW 80MW 

Test Date 2/1/2013 2/1/2013 

Start Time 9:10 11 :05 

Stop Time 10:34 12:15 

Fuel Flow, hscfh 6,912 6,936 

Stack Flow Rate, dscfm 306,797 301 ,392 

Stack 0, (%) 13.47 13.32 13.39 

Stack NOx (ppm) @ 15% 0, 2.27 2.16 2.22 2.5 

Stack NOx (lbIMMscf) 9.23 8.78 9.01 12,261') 

Stack CO (ppm) @ 15% 0, 0.38 0.67 0.52 4 

Moisture Fraction (%) 0.093 0.101 

PPM NH3 (flue gas) 1.20 1.29 1.25 

PPM NH3 @ 15% 0, 0.95 1.00 0.98 5 

Ib/hr NH3 099 1.05 1.02 

Ib/MMscf fuel NH3 1.43 1.51 1.47 

Stack ROGI1 ), ppm @ 15% 0, 0.55 0.55 2.0 

1) Collected as a simultaneous pair. 

2) The 12.26 Ib/MMscf is a RECLAIM emission factor, not a limit. 

R0410673 19 
Test Number 

Condition 

Test Date 

Start Time 

Stop Time 

Fuel Flow, hscfh 

Stack Flow Rate, dscfm 

Stack 0" % 

Stack CO" % 

Moisture Fraction, % 

Particulate Emissions 

Grain Loading, gr/dscf 

Grain Loading @ 3% 0, 

Grain Loading @ 15% 0, 

TABLE 4-4 

COMPLIANCE TEST RESULTS 

CPV SENTINEL ENERGY PROJECT 

SENTINEL UNIT 2 

PM -75% LOAD 

FEBRUARY 1, 2013 

S-2/STK-PM-75-1 

80MW 

2/1/2013 

8:11 

13:22 

6,923 

314,715 

13.35 

4.26 

0.090 

0.0002 

0.0004 

0.0001 

Average 

0.0002 

0.0004 

0.0001 

Grain Loading @ 12% CO, 0.0005 0.0005 

Mass Emissions, Ib/hr 0.49 0.49 

Emission Rate, Ib/MMscf 0.71 0.71 

(1) 11 Ib/hr PM limit from SCAQMD Rule 475. 

(2) This is stated in the permit as an emission factor. 

R041 0673 20 

Limit 

0.01 

0.1 

11 (1) 

5.71(2) 
TABLE 4-5 

COMPLIANCE TEST RESULTS 

CPV SENTINEL ENERGY PROJECT 

SENTINEL UNIT 2 

NO., CO, NH3, AND ROG 

50% LOAD 

FEBRUARY 1, 2013 

Test Number Run 1 Run 2 Average Limit 

Condition 55MW 56MW 

Test Date 2/1/2013 2/1/2013 

Start Time 14:20 15:53 

Stop Time 15:35 17:09 

Fuel Flow, hscfh 5,361 5,391 

Stack Flow Rate, dscfm 282 ,277 278,356 

Stack 0, (%) 14.38 14.36 14.37 

Stack NO, (ppm) @ 15% 0, 1.99 2.05 2.02 2.5 

Stack NO, (lb/MMSCF) 8.44 8.52 8.48 12.261') 

Stack CO (ppm) @ 15% 0, 0.23 0.27 0.25 4 

Moisture Fraction (%) 0.092 0.095 

PPM NH3 (flue gas) 0.72 0.89 0.81 

PPM NH, @ 15% 0, 0.65 0.81 0.73 5 

Ib/hr NH3 0.55 0.67 0.61 

Ib/MMscf fuel NH3 1.02 1.24 1.13 

Stack ROGI1 ), ppm @ 15% 0, 0.68 0.68 2.0 

1) Collected as a simultaneous pair. 

2) The 12.26 Ib/MMscf is a RECLAIM emission factor, not a limit. 

R0410673 21 Deltal1 .. """"' ........ , ... _ .....
TABLE 4-6 

COMPLIANCE TEST RESULTS 

CPV SENTINEL ENERGY PROJECT 

SENTINEL UNIT 2 

PM -50% LOAD 

FEBRUARY 1, 2013 

Test Number S-2/STK-PM-50-1 Average Limit 

Condition 55MW 

Test Date 2/1/2013 

Start Time 14:14 

Stop Time 18:25 

Fuel Flow, hscfh 5,373 

Stack Flow Rate, dscfm 292,783 

Stack 0" % 14.29 

Stack CO" % 3.80 

Moisture Fraction, % 0.075 

Particulate Emissions 

Grain Loading , gr/dscf 0.0002 0.0002 

Grain Loading @ 3% 0, 0.0005 0.0005 0.01 

Grain Loading @ 15% 0, 0.0001 0.0001 

Grain Loading @ 12% CO, 0.0005 0.0005 0.1 

Mass Emissions, Ib/hr 0.42 0.42 11 (1) 

Emission Rate, Ib/MMscf 0.78 0.78 5.711') 

(1) 11 Ib/hr PM limit from SCAQMD Rule 475. 

(2) This is stated in the permit as an emission factor. 

R0410673 22 
R041 0673 

Test Number 

Condition 

Test Date 

SO,, Ib/MMBtu 

gr H,S/100 scI 

TABLE 4-7 

COMPLIANCE TEST RESULTS 

CPV SENTINEL ENERGY PROJECT 

SENTINEL UNIT 2 

SOx FROM FUEL ANALYSIS 

FEBRUARY 1, 2013 

Average 

101 MW 

2/1/2013 

0.00003 

0.013 

Limit 

0.06 

(1) 0.25 gr H,S/100 scf sulfur content limit is based on annual average of monthly 

sample results. 

23 
5.0 DISCUSSION AND TEST CRITIQUE 

Testing was conducted according to the test plan and reference methods. All 

tests demonstrated compliance with the permit limits. The following should be noted: 

• Two runs were conducted for NOx and CO at each condition to ensure that 

sufficient valid data were collected. 

• The ROG test at 100% load did not meet the relative percent difference (RDP) 

criteria specified in SCAQMD Method 25.3 for duplicate canisters. The RDP for 

this test was 23.9% with the criteria being less than 20%. 

• One run was not detected and reported at the PQL level. 

It is not stated if the SCAQMD 25.3 criteria for RDP apply to the procedures 

accepted for modified Method 25.3 approved in the test plan. 

Each canister separately met the permit limit of 2.0 ppm @ 15% O2 . The higher 

ROG result was 0.75 ppm @ 15% O2. The lower ROG result was 0.46 ppm @ 15% O2 . 

The higher of the two results is presented in Tables 1-1 and Table 4-1. 

R0410673 24 Della/}. "'_ ... , .. _ .... 
APPENDIX A QUALITY ASSURANCE 

R041 0673 A-1 Oe/tai"J. """"""<" '"'-
Appendix A.1 Quality Assurance Program Summary 

R0410673 A-2 Del/at... .. _ ..................... 
QUALITY ASSURANCE PROGRAM SUMMARY 

Delta Air Quality Services, Inc. is committed to providing emission related data 

which is complete, precise, accurate, representative, and comparable. Delta's quality 

assurance program and procedures are designed to ensure that the data meet or exceed 

the requirements of each test method for each of these items. The quality assurance 

program consists of the following items: 

• Assignment of an Internal QA Officer 

• Development and use of an internal QA Manual 

• Personnel training 

• Equipment maintenance and calibration 

• Knowledge of current test methods 

• Chain-of-custody 

• QA reviews of test programs 

Assignment of an Internal QA Officer: Delta has assigned an internal QA Officer who is 

responsible for administering all aspects of the QA program. 

Internal Quality Assurance Manual: Delta has prepared a QA Manual according to the 

guidelines issued by EPA. The manual documents and formalizes all of Delta's QA 

efforts. The manual is a "living" document which is revised as Delta adds capabilities and 

procedures. The QA manual provides details on the items provided in this summary. 

Personnel Training: Personnel training is essential to the production of high quality test 

results. Delta's training programs include: 

• A requirement for all technical personnel to read and understand the test 

methods performed 

• A requirement for all technical personnel to read and understand the Delta QA 

manual 

• In-house training 

• Quality Assurance meetings 

• Attendance at EPA sponsored training courses 

• Maintenance of training records. 

Equipment Maintenance and Calibration: All laboratory and field equipment used as a 

part of Delta's emission measurement programs is maintained according to 

manufacturer's recommendations. A summary of the major equipment maintenance 

schedules is summarized in Table A-i. In addition to routine maintenance, calibrations 

are performed on all sampling equipment according to the procedures outlined in the 

applicable test method. The calibration intervals and techniques for major equipment 

components is summarized in Table A-2. 

Knowledge of Current Test Methods: Delta maintains current copies of EPA, ARB, and 

SCAQMD Source Test Manuals and Rules and Regulations. Delta personnel coordinate, 

attend, and present papers at emission testing related conferences. Delta personnel 

maintain memberships in the Air and Waste Management Association and Source 

R0410673 A-3 
Evaluation Society. Delta personnel continually work with industry and regulatory 

agencies in monitoring and developing new methods and rules. 

Chain-of-Custody: Delta maintains chain-of-custody documentation on all data sheets 

and samples. Samples are stored in a locked area accessible only to Delta source test 

personnel. Data sheets are kept in the custody of the originator, program manager, or in 

locked storage until return to Delta's office. Upon return to the office, copies are made 

and stored in a locking file. The original data sheets are used for report preparation and 

any additions are initialed and dated. 

QA Reviews: Every Delta report is reviewed by someone separate from the report 

author. The reviewer is selected based on knowledge of the test methods used and the 

source tested. Periodic field, laboratory, and report reviews are performed by the QA 

Officer. Test plans are reviewed to ensure proper test methods are selected and reports 

are reviewed to ensure that the methods were followed and any deviations from the 

methods are justified and documented. 

R0410673 A-4 
TABLE A-1 

EQUIPMENT MAINTENANCE SCHEDULE 

Equipment Acceptance Limits Frequency of Service Methods of Service 

Pumps 1. Absence of leaks Every 500 hours of 1. Visual inspection 

2. Ability to draw operation or 6 months, 2. Clean 

manufacturers whichever is less 3. Replace parts 

required vacuum 4. Leak check 

and flow 

Flow Meters 1. Free mechanical Every 500 hours of 1. Visual inspection 

movement operation or 6 months, 2. Clean 

whichever is less 3. Calibrate 

Sampling Instruments 1. Absence of As recommended by As recommended by 

malfunction manufacturer manufacturer 

2. Proper response to 

zero, span gas 

Integrated sampling 1. Absence of leaks Depends on nature of 1. Steam clean 

tanks use 2. Leak check 

Mobile van sampling 1 . Absence of leaks Depends on nature of 1. Change filters 

system use 2. Change gas dryer 

3. Leak check 

4. Check for system 

contamination 

Sampling lines 1. Sample After each test series 1. Blow dry, inert gas 

degradation less through line until 

than 2% dry. 

R0410673 A-5 Oeltal1 .. - .. 
TABLE A-2 

MAJOR SAMPLING EQUIPMENT CALIBRATION REQUIREMENTS 

Sampling Equipment Calibration Frequency Calibration Procedure Acceptable Calibration 

Criteria 

Continuous Analyzers Before and after each 3-point calibration error < 2% of analyzer range 

test day test 

Continuous Analyzers Before and after each 2-point sample system < 5% of analyzer range 

test run bias check 

Continuous Analyzers After each test run 2-point analyzer drift < 3% of analyzer range 

determination 

CEMS System Beginning of each day leak check < 1 in. Hg decrease in 5 

min. at > 20 in. Hg 

Continuous Analyzers Daily 3-point linearity < 1 % of analyzer range 

NO, Analyzer Daily N02 -> NO converter > 90% 

efficiency 

S-type pitot tube Semi-annually Dimensional calibration Meet dimensional 

criteria of Method 2 

S-type pitot tube Annually Wind tunnel calibration Defined in Method 2 

S-type pitot tube Prior to each project Visual inspection Meet dimensional 

criteria of Method 2 

Differential Pressure Semi-annually Correction factor based +/- 5% 

Gauges (except for on 5-point comparison to 

manometers) standard 

Differential Pressure Bi-monthly 3-point comparison to +/- 5% 

Gauges (except for standard, no correction 

manometers) factor 

Manometer Semi-annually Clean and replace fluid 

Barometer Semi-annually Adjusted to mercury-in- +/- 0.1 inches Hg 

glass or National 

Weather Service Station 

Dry gas meter Semi-annually Calibration check at 4 +/- 2% 

flow rates using a N 1ST 

traceable standard 

Dry gas meter Bi-monthly Calibration check at 2 +/- 2% of semi-annual 

flow rates using a N 1ST factor 

traceable standard 

Dry gas meter orifice Annually 4-point calibration for 

IIH@ 

Temperature sensors Semi-annually 3-point calibration vs. +/- 1.5% 

NIST traceable standard 

R041 0673 A-6 
Appendix A.2 SCAQMD and CARB Certifications 

R0410673 A-7 "'0.-, Delta ......... __ /1 
South Coast 

Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

(909) 396-2000 • www.aqmd.gov 

Mr. Robert A. Finken 

Delta Air Quality Services, Inc. 

1845 N. Case Street 

Orange, CA 92865 

Subject: LAP Approval Notice 

Reference # 96LAI220 

Dear Mr. Finken: 

January 11, 2012 

We completed our review of the renewal application you submitted for approval under the South Coast 

Air Quality Management District's Laboratory Approval Program (AQMD LAP). We are pleased to 

inform you that your firm is approved for the period beginning January 31, 2012, and ending January 31, 

2013 for the following methods: 

SCAQMD Methods 1-4 

SCAQMD Method 100.1 

SCAQMD Methods 25.1 and 25.3 (Sampling) 

SCAQMD Methods 5.1, 5.2, 5.3, and 6.1 

SCAQMD Rule 1420 - (Lead) Ambient Sampling 

USEPA CTM-030 and ASTM D6522-00 

Thank you for participating in the SCAQMD LAP. Your cooperation helps us to achieve the goal of the 

LAP: to maintain high standards of quality in the sampling and analysis of source emissions. You may 

direct any questions or information to LAP Coordinator, Glenn Kasai. He may be reached by telephone 

at (909) 396-2271, by facsimilie at (909) 396-2099, or via e-mail at gkasai@aqrnd.gov . 

RE:GKlgk 

cc: Mike Garibay 

Glenn Kasai 

120111 LapRenewaJ.doc 

. 't''',. , ~nr/,y ~ ___ _ 

;/ Ru Eden, Senior Manager 

Laboratory Services & 

Source Test Engineering 
South Coast 

Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

(909) 396-2000 • www.aqmd.gov 

December 19,2012 

Mr. Robert A. Finken 

Delta Air Quality Services, Inc. 

1845 N. Case Street 

Orange, CA 92865 

Subject: LAP Approval Notice 

Reference # 96LA 1220 

Dear Mr. Finken: 

We completed our review of the renewal application you submitted for approval under the South Coast 

Air Quality Management District's Laboratory Approval Program (AQMD LAP). We are pleased to 

inform you that your firm is approved for the period beginning January 31, 2013, and ending January 31, 

2014 for the following methods, subject to the requirements in the LAP Conditions For Approval 

Agreement and conditions listed in the attachment to this letter: 

SCAQMD Methods 1-4 

SCAQMD Method 100.1 

SCAQMD Methods 25.1 and 25.3 (Sampling) 

SCAQMD Methods 5.1 , 5.2, 5.3, and 6.1 

SCAQMD Rule 1420 - (Lead) Ambient Sampling 

US EPA CTM-030 and ASTM D6522-00 

Thank you for participating in the SCAQMD LAP. Your cooperation helps us to achieve the goal of the 

LAP: to maintain high standards of quality in the sampling and analysis of source emissions. You may 

direct any questions or information to LAP Coordinator, Glenn Kasai. He may be reached by telephone 

at (909) 396-2271, by facsimilie at (909) 396-2099, or via e-mail at gkasai@aqmd.gov. 

RE:GKlgk 

cc: Mike Garibay 

Glenn Kasai 

121218 LapRenewal.doc 

~ R,dy 

Laboratory 

po" 

Services 

s,,~ & 

Source Test Engineering 
State of California 

Air Resources Board 

Approved Independent Contractor 

Delta Air Quality Servic~~ Incorporated 

, . , 

This is to certify thitt the company'Jisted above has been approved 

by the AirHesources Board to conduCt:pom~pl\ance testing 

pursuant to titleH7, Catifomla Coqe 6fR~gu1ations. section 91207 

until June 30, 2013, for thO~e test metnoUs Ii$ted below: 

~: il 

.ARB sliurce Test M~th"ods: 

1~ 2, 3, 4,"5, 6,'S, 17, 20,sqt 

100'(CQ. CO2, NO .. O,.l. S02) . ~ , 

Alberto Aya~, PhD., M.S.E. 

Chief, Monitoring and Laboratory Division 
State of California 

Air Resources Board 

Delta A)W1f~JifY ~e!v.i.~~}'IR~~tPora 

This is to f'ArHhlftH":::If. 

by the 

pursuan~ to ~i~~IT~isa~ 

until JU!1~ 2q>J'il2tY1:~ 

u.s. 

n approved 

testing 

section 91207 

1;l~~ I, ~~~~~<fr~j~d below: •. " 7/./0, I, "T! I. I 

.L\I~:~1}" l version) 

Alberto Ayala, 9fl.D., M.S.E. 

Chief, Monitoring and Laboratory Division 
Appendix A.3 Equipment Calibration and Calibration Gas Certificates 

R0410673 A-8 

Deltaj'j, ......... _,""--" 
Ofifice Method· Triplicate RunsIFour Calibration Points 

Engtish Meter Bo)( Units, English K' Factor 

SEMI·ANNUAL DRY GAS METER/ORIFICE CALIBRATION 

Filename' F'\compdat!l\Oe1ta P1.Iblic\CatibraMns\MelefS\19-wcs12012\[Semi·Annual Meier Calibration 19 wcs 1()'2S·12.)(\sjWCS 

MO<IeI #. 

10 , 

Dale' 

~5000 

19·wcs 

1012512012 

File Modified From. APEX 522 Series Meter box Cal bra~on 

Revised: 418/2005 

Volume Volume 

dH Time Initial Final 

(in H2O) (min) {cu ttl (cu tt) 

0.13 26.00 351.800 357,170 

0.13 26,00 357.170 362.550 

0.13 26.00 362.550 367.942 

066 12,00 367.942 373.425 

066 12,00 373.425 378.895 

066 12.00 378.895 384,378 

1.90 7.00 384.378 389.855 

1.90 7.00 389.855 395340 

190 7.00 395.340 400.829 

3.70 5.00 "00.829 406.200 

3.70 5.00 "06.200 411.586 

3.70 500 "" .586 416995 

METER ORIFICE 

VOLUME VOLUME VOLUME 

CORRECTED CORRECTED CORRECTED 

Vm(std) Vm(std) Vcr(sld) 

w" liters (cu ttl 

5,406 153.1 5.265 

5,400 152.9 5,265 

5,397 152.8 5.265 

5.479 155.2 5.422 

5459 154.6 5.419 

5.469 154.9 5.4 17 

5.472 155.0 5.369 

5.470 154.9 5.369 

5.466 154.6 5.367 

5.367 152.0 5.338 

5372 152.1 5.336 

5387 152.6 5338 

SIGNED Signature on File 

Bar. Pressure: 29.65 

Performed By: G. Bridge 

Meter Senal #; 

DRY GAS METER READINGS CRITICAL ORIFICE READINGS 

Volume Initial Temps. Final Temps. Orifice K' Orifice Actual 

Total Inlet Outlet Inlel Outlet Serial# Coefficienl Vacuum 

('" ') (deg F) (deg F) (deg F) (deg F) (number) (see above) (in Hg) 

5,370 63.0 62.0 65.0 63.0 33 0.1553 26.0 

5.380 65.0 63.0 67.0 64.0 33 0.1553 26.0 

5.392 67,0 64.0 68.0 66.0 33 01553 26.0 

5.483 68.0 66.0 70.0 67.0 " 0.3465 22,5 

5470 70,0 67.0 70.0 67.0 I " 0.3465 22,5 

5483 70.0 67.0 70.0 68.0 " 0.3465 22,5 

5477 70.0 68.0 72.0 68.0 " 0.5888 19.5 

5485 72.0 68.0 73.0 69.0 " 0.5888 19.5 

5489 73.0 69.0 7" .0 69.0 63 0.5888 195 

5371 7" 69.0 750 69.0 73 0.8202 17.0 

5386 750 69.0 77.0 70.0 73 0.8202 17.0 

5.4()9 77.0 70.0 77.0 70.0 I 73 08202 17.0 

DRY GAS METER ORIFICE 

CALIBRATION FACTOR CALIBRATION FACTOR Individual 

VOLUME VOLUME Roo 

CORRECTED NOMINAL Y dH@ 

Vcr(std) Vee Value Value 0.95 < Y 

liters '" " (number) in H2O < 1.05? 

1491 5240 1.798 Pass 

149.1 5,240 1.794 Pus 

149.1 5,240 1.789 Pass 

Average 1.794 

1536 5396 0990 1.819 P 

1535 5398 0,993 1,619 Pass 

1534 5.401 0.990 1,619 Pass 

Average 0.991 1.819 

152.1 53" 0981 1.812 P 

1521 53" 0982 1.610 Pass 

1520 5.356 0 .982 1.610 Pass 

Average 0.982 1.811 

1512 5332 0.995 1.819 P 

1512 5332 0.994 1.817 Pass 

1512 5332 0991 1.815 Pass 

'---'AO~'"';;;;ge Vd: 0.985 dH@:1.810 

Q@dH=I : 0.557 

Date 1012512012 

(In. Hg) 

Initial 

(deg F) 

64.0 

64,0 

64.0 

64.0 

64.0 

65.0 

65.0 

65.0 

65.0 

66.0 

66.0 

66.0 

Individual 

OrifICe 

Ymax ·Ymin 

< 0.010? 

Pass 

Pass 

Pass 

Ambient Temperature 

Final Average 

(d'9 ') (d'9 ') 

64.0 64.0 

64.0 64.0 

64.0 64.0 

64.0 640 

65.0 64.5 

65.0 65.0 

65.0 650 

65.0 650 

66.0 655 

66.0 660 

66.0 660 

66.0 660 

Orifice Ofifice 

Average Average 

0.98 < YrYd dH@ · dH@av 

< I.on < 0.155? 

Pass Pass 

Pass Pass 

Pass Pass 

Sem~Anooa l MeIer Calibfalloo 19 wei 10·25·12 WCS 

211912013 

157 PM 
Orifice Method - Triplicate RunsIFour Calibration Points 

English Meter Box Units, English K' Factor 

SEMI·ANNUAL DRY GAS METER/ORIFICE CALIBRATION 

Model #: 

10#: 

Filel"lilme: F \compdata\Oelta Public\CalibratiooslMeters\9-P&M\2012I{Semi-Annual Meter Calibration -9-pm 9-21-12.xlsIWCS Dale: 

9P&M 

912112012 

File Modified From' APEX 522 Series Meter box Calibration 

Revised: 41812005 

Volume Volume 

dH Time Initial Final 

in H2O} (min) {cu ttl (cu 11) 

0. 14 2600 383,400 388.805 

0.14 26.00 388,805 394.205 

0.14 26.00 394,205 399.6 15 

0.64 12.00 350,820 356.270 

0.64 12.00 356,270 361 .730 

0.64 1200 361,730 367.175 

1.90 700 367.175 372.585 

190 700 372.585 377.990 

190 7.00 377 990 383.400 

3.70 5.00 334.700 340.065 

3.70 500 340.065 345.430 

370 500 345.430 350 810 

DRY GAS METER 

VOLUME VOLUME VOLUME 

CORRECTED CORRECTED CORRECTED 

Vm(sld) Vm(std) Vcr(std) 

(cu tt) liters) (eu 11) 

5.269 1492 5.176 

5.254 148,8 5.171 

5.254 148.6 5.1 67 

5,354 1516 5.343 

5.359 151.8 5.340 

5334 1511 5.335 

5.311 150.4 5.286 

53<12 lSO.1 5.284 

53<12 1SO 1 5.281 

5.330 1510 5277 

5320 lSO.7 5.274 

5.330 1510 5274 

SIGNED: Signature on File 

Bar. Pressure. 

Performed By: 

29.72 {in. H9} 

M. Edmondson 

DRY GAS METER READINGS CRITICAL ORIFICE READINGS 

Volume Inllial Temps Final Temps Orifice K' Orifice Actual 

Total Inlet Outlel Inlel Outlet Serial# Coefficient Vacuum Initial 

"''' Idea Fl dea F) (dea F) (de<! F) {number (see above) in Ha) (dea F) 

5.405 78.0 770 79.0 78,0 33 0,1553 23.0 770 

5.400 79,0 78.0 80.0 79,0 33 0,1553 23.0 78,0 

5.410 80,0 790 81.0 80,0 33 0.1553 23.0 79,0 

5.450 75,0 74.0 75.0 74,0 " 0.3465 20.0 75,0 

5.460 I 750 74.0 76.0 75,0 I " 0,3465 20.0 75,0 

5.445 76.0 750 770 76,0 48 0,3465 200 76.0 

5.410 770 76.0 77.0 760 I 63 05888 17.0 77.0 

5.405 77.0 76.0 78.0 77.0 63 0.5888 17.0 77.0 

5410 78.0 770 78.0 77.0 63 0.5888 170 78.0 

5.365 720 720 73.0 730 73 0.8202 150 73.0 

5.365 730 730 740 740 73 0.8202 15.0 740 

5380 74.0 740 740 74.0 73 08202 15.0 74.0 

ORIFICE DRY GAS METER ORIFICE 

CALlBRA TlON FACTOR CALlBRATION FACTOR Individual Individual 

VOLUME VOLUME Roo Orifice 

CORRECTED NOMINAL Y dH@ 

VCf(std) Vcr Value Value 0,95 < Y Yma)( - Ymin 

liters) i'" ") (number) (in H2O) , < 1.05? < O,OI 0? 

146.6 5.307 0,982 1.939 Pass 

1465 5,312 0.984 1.939 Pass 

146.3 5.3 17 0.983 1.939 Pass 

Average 0.983 1.939 Pass 

151.3 5452 0.998 1784 Pass 

151.2 5455 0997 1,784 Pass 

151 1 5.460 1.000 1,784 Pass 

Average 0.998 1.184 Pass 

1497 541 4 0.995 1.834 Pass 

1496 5417 0997 1.834 Pass 

1496 5 419 0996 1.834 Pass 

Averag4i! 0.996 1.834 Pass 

1494 5.370 0990 1.840 Pass 

14g 4 5372 0.991 1.839 Pass 

149.4 5.372 0990 1.837 Pass 

Average 0.990 1.839 Pass 

Average Yd: 0.992 dH@: 1.849 

Q@dH:l : 0.552 

Date: 912112012 

Ambient Temperature 

Final Average 

(dea F) "eo Fl 78,0 77.5 

79.0 78.5 

80.0 79.5 

75.0 750 

76.0 75,5 

770 76,5 

77.0 770 

78.0 77.5 

78.0 78,0 

74.0 735 

74.0 74.0 

74.0 74.0 

Orifice Onfice 

Average Average 

0.98 < Yf'(d dH@-dH@av 

< 1.02? < 0.1557 

Pass Pass 

Pass Pass 

Pass Pass 

Pass Pass 

~mi·Armu.' Me1e' C.lib,,,ion 9·~m 9·21 -12 WCS 

2/1912013 

158 PM 
Orifice Method - Triplicate RunslFol1f Calibration POints 

English Meier Box Units. English K' Factor 

SEMI·ANNUAl DRY GAS METER/ORIFICE CALIBRATION 

Model #. 

lOti. 

C5000 

17WCS 

Filename. F:lcompdata\Oelta Public\Calibrations\Meters\17-wcs\2012\jSeml-AAnual Metei' Calibration 9-19-12 WCSJds]WCS Date 911912012 

file Modified From: APEX 522 Senes Meter box Calibration Bar. Pressure 29.79 (in. Hg) 

Revised: 4/812005 PerlOfl'ned By. :;ARY BRIDGE 

DRY GAS METER READINGS CRITICAL ORifiCE READINGS 

Volume Volume Volume Inilial Temps. Final Temps Orifice K' Orifice Actual 

dH Time Initial Final Total Inlet Oullet Inlet Ou~et Serial# Coefficient Vacuum Initial 

(in H2O) (min) {eu ttl (eu ttl (eu ttl "eo F) "eo F) "eo F) (deo F) (number) (see above) (in Hg) (deg F) 

0.1 1 26.00 368.900 374,275 I 5,375 74,0 73,0 I 74.0 73.0 33 0.1553 23,5 730 

0.11 26,00 374.275 379.658 5.383 74 ,0 73,0 77.0 75.0 33 0.1553 23,5 73,0 

0.11 26,00 380.200 385.581 5.381 77.0 75,0 77.0 75.0 33 0.1553 23.5 73,0 

0.55 12,00 389.200 394.650 5.450 73,0 730 74.0 73.0 48 0.3465 200 74.0 

0.55 1200 394.650 400.128 5478 74,0 73,0 75.0 74.0 " 0.3465 20,0 74.0 

0.55 12.00 400.128 405.593 5.465 75,0 74.0 76.0 74.0 " 0.3465 20.0 74.0 

1.70 7.00 405.593 411.028 5435 76.0 "0 77.0 75.0 " 0.5888 \65 74.0 

1.70 7.00 411 .028 416.485 5457 77.0 750 78.0 75.0 " 0.5888 16.5 74.0 

1.70 7.00 416.485 421.937 5.452 760 75.0 79.0 76.0 " 0.5888 '65 74.0 

3.30 500 421 .937 427.253 5.316 790 760 81 .0 76.0 73 08202 13.0 74.0 

3.30 5.00 427.253 432.550 5.297 8" 760 82.0 76.0 73 0.8202 13.0 74.0 

3.30 5.00 432.550 437.886 5336 820 76.0 83.0 77.0 73 0.8202 13.0 74.0 

DRY GAS METER ORIFICE DRY GAS METER ORifiCE 

CALIBRATION FACTOR CALIBRATION fACTOR Individual Individual 

VOLUME VOLUME VOLUME VOLUME VOLUME Roo Orifice 

CORRECTED CORRECTED CORRECTED CORRECTED NOMINAL Y dH@ 

Vm(sld) Vm(sld) Ver(std) Ver(std) V" Value Value 0.95" Y Ymax - Ymin 

(eu tt) . (liters) (eu tt) (liters leu ttl number) (in H2O) < 1.05? < O.O'O? 

5.296 150.0 5,210 147,6 5285 0.984 1,520 Pass 

5.291 149.8 5.2 10 147.6 5.285 0.985 1.517 Pass 

5.277 149.4 5.208 147.5 5287 0.987 1,515 Pass 

Average 0.985 1.517 Pass 

5378 152.3 5.360 151 .8 5447 0,997 1 529 Pass 

5.398 152,9 5,360 151 8 5447 0993 1,528 Pass 

5.378 1523 5.360 151 e 5447 0997 1,526 Pass 

Average 0.995 1.528 Pass 

5.356 151 7 5.313 1505 5399 0.992 1632 PlISS 

5.370 1521 5.313 1505 5.399 0.989 1631 Pass 

5.358 151.7 5.313 '505 5.399 0992 1629 Pass 

Averag4 0.991 1.631 Pass 

5.235 148.2 5.287 1497 5.372 1.010 1628 Pass 

5209 147.5 5.287 1497 5 372 1.015 1.628 Pass 

5.240 1484 52'" 1497 5375 ' .006 1628 Pass 

Average 1.011 1.628 Pass 

1

---- Average Yd: 0.996 dH@: 1.576 

Q@dH"l : 0.597 

SIGNED Date. 

Ambient Temperature 

Final Average 

(deg f) "eo F) 73.0 73.0 

73.0 730 

74.0 73.5 

74.0 "0 

74.0 74.0 

74.0 74.0 

74.0 7" 

74.0 74.0 

74.0 74.0 

74.0 "0 

74.0 7" 

75.0 7" 

Orifice OrifICe 

Average Average 

0.98" YfYd dH@ -dH@ av 

" 1.02? 

Pass 

Pass 

Pass 

Pass 

.. 0, 155? 

Pass 

Pass 

i 

i 

, 

Pass , 

, 

Pass 

Sem~AMual Meter Cillbrilion 9·1 9-12 WCI WCS 

211MQ13 

t S6 PM 
Standard Pitot Tube Dimensional Calibration Record 

A 

,------ - @ A 

M Stclion AA 

• 

T 

Tip 

ccep,al}l I Y 

Criteria Yo; Y., 0'. ",. 0" ro. -0.101 M1 >6 01 M2 >8 01 

Hemispherical, 90· Bend with 

PitotlO Date Calibrated B Elliptical, or curved or mitered 01 02 ., .2 Ratio 02/01 601 801 Status 

Conical Tip unction 

8 y Y 0.31 0.029 2.110 2.550 0.094 1.860 2.5 Pass 
5 Type Pitot Tube Dimensional Calibration Record 

Side View 

,LW 

f ~ M, ~ 

1 

= __ --c A B3tr , 

End View 

Acceptability "3/16" < Dt < 

Criteria z < 1/8" w < 1132" y" 3/8" nla nla nla nla nla 

Side View, Side View, 

Impact Impact 

Pitot ID Date Calibrated By openings openings Pa: Pb Tubing Mt M2 M3 M4 M. Properly Properly Diameter, dt 

aligned, Z < aligned, w 

1/8" < 1132" 

026 Y Y Y 0.374 0.882 0.870 0.882 0.876 0.437 --_. -

Reference "A Type-S Pilot Tube Calibration Study, Robert F. Vollaro, October 15, 1975 

If tube is not visibly deformed it is assumed that Pa = Pb = .5 x avg. of M1 M2, and that average face opening plane angles represent individual angles to tube axis 

M. 

nla 

M. 

0.457 

-+/ M, r-

;. §( P:b t - ,- M

M, : 

Pa 

• 1 

-+1 

Too View 

~ 

1.0SDt<P<1.S 

10 degrees 5 degrees Dt 

Average Face Average Face Opening Plane 

Angle, offset Opening Plane 

from Frontal Angle Ratio of PlOt Status 

perpendicular from parallel to 

to transverse Longitudinal 

axis Axis 

0.9 0.4 1.2 Pass -
OIL 

WATER 

PTC-10 

PTC-10 

361 

212 

TEMPERATURE SYSTEM CALIBRATION 

STANDARD 

361 

212 

361 

212 

#8 

361 

212 

360 

212 

360 

212 

360 

212 

360 

212 

0.1% Pess 

o 0.0% Pass 

F--"~ ____ ~~~ __ ~~ __ ~~ ____ ~;-____ ~~+-~~ __ ~ ____ ~~ __ ~~-f __ ~ ____ ~~,pass 

OIL PTC-11 362 362 362 362 360 360 360 360 Pass 

WATER PTC-11 213 213 213 213 212 212 212 212 

WATER 

OIL 

WATER 

OIL 

WATER 

PTC-22 

PTC-23 

PTC-23 

PTC-24 

PTC-24 

360 

214 

361 

213 

Calibrated By: DMW. RM. RMO, DA, ME 

360 

214 

361 

213 

360 

214 

361 

213 

360 

214 

361 

213 

360 

212 

360 

212 

212 

360 

212 

360 

212 

360 

212 

360 

212 

360 

212 

360 

212 

o 

2 

January 2, 2013 
Reference Thermometer I D.: 

TIC Readout 

t.o. I D. 

'" Readina 1 

OIL PTC·25 362 

WATER PTC·25 213 

ICE PTC·25 32 

OIL PTC·26 362 

WATER PTC·26 212 

ICE PTC·26 31 

OIL PTC·27 363 

WATER PTC·27 213 

ICE PTC·27 30 

OIL PTC·2S 362 

WATER PTC-28 212 

ICE PTC-28 30 

OIL PTC·29 361 

WATER PTC-29 211 

ICE PTC-29 31 

OIL PTC-30 361 

WATER PTC-30 212 

ICE PTC-30 31 

OIL TRO-l 361 

WATER TRO·l 212 

ICE TRO·l 33 

OIL TRO-4 362 

WATER TRO-4 211 

ICE TRO-4 32 

OIL TRO-5 362 

WATER TRO-5 214 

ICE TRO-5 32 

OIL TRO..e 362 

WATER TRO..e 212 

ICE TRO..e 31 

OIL TRO-8 362 

WATER TRO·S 213 

ICE TRO·S 35 

OIL TRO-9 361 

WATER TRO·9 212 

ICE TRO-9 32 

OIL TRO·ll 360 

WATER TRO-l1 214 

ICE TRO-ll 31 

OIL TRO·12 360 

WATER TRO-12 213 

ICE TRO-12 32 

OIL TRO-13 361 

WATER TRO-13 212 

ICE TRO-13 31 

OIL TRO-1S 364 

WATER TRO·1S 213 

ICE TRO·1S 31 

OIL TRO·16 364 

WATER TRO-16 212 

ICE TRO-16 32 

OIL TRO·1S 362 

WATER TRO-IS 213 

ICE TRO-IS 32 

OIL TRO-19 363 

WATER TRO-19 213 

ICE TRO-19 31 

OIL TRO-20 364 

WATER TRO·20 212 

ICE TRO·20 33 

OIL TRO·22 363 

WATER TRO-22 213 

ICE TRO-22 31 

OIL TRO·23 362 

WATER TRO-23 212 

ICE TRO-23 31 

OIL TRO-24 362 

WATER TRO-24 213 

ICE TRO-24 32 

T1 

TEMPERATURE SYSTEM CALIBRATION 

STYPE 

#26 F9~195 T2 F95·195 T3 F9~195 

TIC . Readout Reference Thermometer 

·F ., Readina 2 Readina 3 Averaae Readina 1 Readina 2 Readina 3 Averaoe 

362 362 362 360 360 360 360 

213 213 213 212 212 212 212 

32 32 32 32 32 32 32 

362 362 362 360 360 360 360 

212 212 212 212 212 212 212 

31 31 31 32 32 32 32 

363 363 363 360 360 360 360 

213 213 213 212 212 212 212 

30 30 30 32 32 32 32 

362 362 362 360 360 360 360 

212 212 212 212 212 212 212 

30 30 30 32 32 32 32 

361 361 361 360 360 360 360 

211 211 211 212 212 212 212 

31 31 31 32 32 32 32 

361 361 361 360 360 360 360 

212 212 212 212 212 212 212 

31 31 31 32 32 32 32 

361 361 361 360 360 360 360 

212 212 212 212 212 212 212 

33 33 33 32 32 32 32 

362 362 362 360 360 360 360 

211 211 211 212 212 212 212 

32 32 32 32 32 32 32 

362 362 362 360 360 360 360 

214 214 21 4 212 212 212 212 

32 32 32 32 32 32 32 

362 362 362 360 360 360 360 

212 212 212 212 212 212 212 

31 31 31 32 32 32 32 

362 362 362 360 360 360 360 

213 213 213 21 2 212 212 212 

35 35 35 32 32 32 32 

361 361 361 360 360 360 360 

212 212 212 212 212 212 212 

32 32 32 32 32 32 32 

360 360 360 360 360 360 360 

21 4 214 21 4 212 212 212 212 

31 31 31 32 32 32 32 

360 360 360 360 360 360 360 

213 213 213 212 212 212 212 

32 32 32 32 32 32 32 

361 361 361 360 360 360 360 

212 212 212 212 212 212 212 

31 31 31 32 32 32 32 

364 364 364 360 360 360 360 

213 213 213 212 212 212 212 

31 31 31 32 32 32 32 

364 364 364 360 360 360 360 

212 212 212 212 212 212 212 

32 32 32 32 32 32 32 

362 362 362 360 360 360 360 

213 213 213 212 212 212 212 

32 32 32 32 32 32 32 

363 363 363 360 360 360 360 

213 213 213 212 212 212 212 

31 31 31 32 32 32 32 

364 364 364 360 360 360 360 

212 212 212 212 212 212 212 

33 33 33 32 32 32 32 

363 363 363 360 360 360 360 

213 213 213 212 212 212 212 

31 31 31 32 32 32 32 

362 362 362 360 360 360 360 

212 212 212 212 212 212 212 

31 31 31 32 32 32 32 

362 362 362 360 360 360 360 

213 213 213 212 212 212 212 

32 32 32 32 32 32 32 

Calibrated By: DMW, RM, RMO, CA, ME 

Differeoce 

·F 

2 

1 

0 

2 

0 

1 

3 

1 

2 

2 

0 

2 

1 

1 

1 

1 

0 

1 

1 

0 

1 

2 

1 

0 

2 

2 

0 

2 

0 

1 

2 

1 

3 

1 

0 

0 

0 

2 

1 

0 

1 

0 

1 

0 

1 

4 

1 

1 

4 

0 

0 

2 

1 

0 

3 

1 

1 

4 

0 

1 

3 

1 

1 

2 

0 

1 

2 

1 

0 

%.("R) 

0.2% 

0.1% 

0.0% 

0.2% 

0.0% 

0.2% 

0.4% 

0.1% 

0.4% 

0.2% 

0.0% 

0.4% 

0.1% 

0.1% 

0.2% 

0.1% 

00% 

02% 

0.1% 

0.0% 

02% 

0.2°'" 

0.1% 

0.0% 

0.2% 

0.3% 

0.0% 

0.2% 

0.0% 

0.2% 

0.2% 

0.1% 

0.6% 

0.1% 

0.0% 

0.0% 

0.0% 

0.3% 

0.2% 

0.0% 

0.1% 

00% 

01% 

0.0% 

0.2% 

0.5% 

0.1% 

0.2% 

0.5% 

0.0% 

0.0% 

0.2% 

0.1% 

0.0% 

0. 4% 

0.1% 

0,2% 

0,5"'" 

0,0% 

0,2% 

04% 

0.1% 

0.2% 

0.2% 

0.0% 

0.2% 

0.2% 

0.1% 

0.0% 

P .n ." 

." 

. n 

. n 

. n 

. n ." 

'" .n 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P .n P 

P 

P 

'" 

'" '" '" 

'" 

.n '" 

P 

P 

P 

P 

P .n 

P .n 

P '" P .n 

P 

P .n '" 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

P 

.n ." ." 

." 

'" '" .n 

'" . n 

'" . n 

.n 

'" '" '" ." 

.n 

.n 

'" '" ." ." 

'" 'n 

'" .n 

.n 

.n 

.n 

.n 

.n 

.n 

.n 

." 

.n 

.n 

.n 

.n 

.n 

.n 

.n ." 

.n 

.n 

.n 

January 2, 2013 
0611811. Air Qualify Services, Incorporated 

NOZZLE CALIBRATION DATA 

Nozzle I.D. ,-)1.,.L.,/ .. vl 1lJ· .J..3 'I 5z ;f1iL Date ,. C).tf. , 3 

Material 55 Bv .I::! ,f? v .. ~-1.. 

Confiauration IL or Hook) I.J,., ,JlC 

Maximum Difference Di - Dj = OC'U:l... (must be 0.004") 

Average Dn = C· J 3 vi 

Note: Measure three diameters with micrometer 

DS934098 

Date of last revision 9/28/2012 Master Document StoragelFormslDatasheetslCalibration Forms 
Appendix A.4 

R041 0673 

Delta CEM System Description and SCAQMD Method 100.1 

Calibration and Test Sequence 

A-9 
SCAQMD METHOD 100.1 CALIBRATION SEQUENCE AND CALCULATIONS 

DEFINITIONS: 

1) Analyzer Calibration: 

2) Calibration Error: 

3) Analyzer Linearity: 

4) Sample System Bias: 

R0410673 

Zero and span gas(es) are introduced directly to the 

analyzer. Adjustments are made to the analyzer zero and 

upscale readings , as necessary to match the certified 

concentrations of the calibration gas. 

Zero, mid (40-60% of full scale), and high (80-100% of full 

scale) calibration gases are introduced directly to the 

analyzer and the analyzer response to each gas is 

recorded (without adjustment to the analyzer). The 

Calibration Error (difference between the analyzer response 

to the calibration gas and the certified concentration of the 

calibration gas) must not exceed ±2% of the analyzer full 

scale for any of the three gases. 

Analyzer linearity is defined as the difference between an 

analyzer response to the mid range gas and the predicted 

analyzer response to the mid range gas based on the 

analyzer response to the zero and high range gas. The 

Analyzer Linearity test is required on a semi-annual basis 

and must not exceed ±1 % of the analyzer range. It should 

be noted that this linearity requirement is more stringent 

than the best available calibration standards (+1-2%) for the 

low CO and NOx concentrations expected during this test 

program. For this reason , an analyzer linearity of less than 

2% will be considered as acceptable for this program. 

The sample system bias test involves introducing zero and 

one upscale (mid or high) calibration gas to the entire 

sampling system and recording the analyzer response. The 

analyzer response to the calibration gas after it has passed 

through the entire sample system is compared to the 

analyzer response to same the calibration gas injected 

directly to the analyzer. The test is used to determine the 

effect which the sample system has on the species of 

interest and correct the measured values for any effect 

which the system has. The sample system bias is required 

to be less than ±5% of the analyzer range for both the zero 

and upscale gas. 

A-10 .!!t!la.4. 
PROCEDURES AND CALCULATIONS: 

Figure 1 presents a flow chart for the SCAQMD Method 100.1 calibration 

sequence. All calibrations are documented as one-minute averages from the reference 

method Data Acquisition System. 

Following assembly of the system, analyzer warm up time, and a successful leak 

check of the sample system, the calibration/test sequence presented in Figure 1 can 

begin. 

An Analyzer Calibration is performed as necessary by adjusting the zero and 

span settings of the analyzer. These calibrations are not necessarily recorded on the 

chart recorder. Calibration Error is then determined at three levels for each range (which 

is expected to be used) of each analyzer. This check is performed, at a minimum, once 

at the beginning and once at the end of each test day. The calibration error must not 

exceed ±2% of the full range of the analyzer as determined by the following equation: 

Calibration Error Analyzer Response- Cal. Gas Value )/ = • 100'10 

Analyzer Range 

The data from the Calibration Error test can be used to determine Analyzer 

Linearity. The analyzer response to the mid gas is predicted using linear regression and 

the analyzer response to the zero and high calibration gas and the zero and high 

calibration gas values . The analyzer linearity must be demonstrated on a semi-annual 

basis using the following equation: 

Analyzer Response - Predicted Response Analyzer Linearity = • 100% 

Analyzer Range 

where: 

Response to High Gas . Response to Zero Gas 

Predicted Response ;: * Mid Gas Value + Response to Zero Gas 

High Gas Value 

The Sample System Bias test is performed before and after each test run and 

must not exceed ±5% of the analyzer range for both the zero and upscale span gas. The 

system bias is calculated using the following equation: 

Response to System Bias - Response to Analyzer Cal Sample System Bias = • 100% Analyzer Range 

R041 0673 A-11 
where: 

Response to Analyzer Cal = The analyzer response to the last time the same 

calibration gas was introduced directly to the analyzer (this may be the pre-test 

calibration error value or a more recent analyzer calibration adjustment) 

Zero and Calibration Drift are calculated for each test run based on the analyzer 

response during the pre- and post-test sample system bias test. Zero and upscale drift 

must not exceed ±3% of the analyzer range. 

I D 'ft Post - Test System Bios Resonse - Pre - Test System Bios Response Ana yzer n = ' 100% 

Analyzer Range 

The pre- and post-test analyzer response during the sample system bias test are 

used to correct the raw test average for any sample system bias and analyzer drift. The 

drift/bias corrected data are the actual reported concentrations and are used for 

subsequent calculations (mass emission rates, Ib/MMBtu, corrections to 3% or 15% O2, 

etc.). The drift/bias corrections is performed using the following equation: 

where: 

Cc = Drift/bias corrected concentration 

C = Raw Test Average 

Cm = Average of pre- and post-test response to sample system bias span 

Co = Average of pre- and post-test to sample system bias zero 

Cma = Span gas value 

ADDITIONAL QUALITY ASSURANCE CHECKS: 

SCAQMD Method 100.1 specifies the allowed analyzer interferences for each 

analyzer type. No interference checks are required for O2 or NO, analyzers. 

Interference tolerances are given for CO, CO2, and S02 analyzers. The analyzers used 

by Delta are certified by the manufacturers to have interference responses which meet 

the requirements of Method 100.1. 

SCAQMD has published a draft method for determining the efficiency of a N02 to 

NO converter. This test will be performed once on the day of the test. The converter 

efficiency must be 90% or greater. 

R041 0673 A-12 Del/al:!.. "' '''''"''' ......... _. 
Analyzer 

Cal 

Cal No 

Error < 2% 

No 

Yes IYes 

System 1\1" System 

Bias < 5% Problem? 

Yes 

Don't Know Stratified No 

Location? 

Yes 

Multi-Point Single Point 

Test Test 

1 

System No 

Bias < 5% 

Yes 

Cal No 

Drift < 3% 

1 Yes 

Note: AQMD policy allows multiple Another 1 No Analyzer Cal test runs 10 be validated by one set I of pre- and post-test sample system Test? (if necessary) 

bias tests as long as the bias 

1 checks are performed within 2 hours Yes 

of the previous bias check. No No 

Analyzer [ Cal 

Cal? Error < 2% lYes 

No 1 Yes 

Yes System [ Finish 

1 Bias < 5% I--

FIGURE 1: SCAQMD METHOD 100.1 CALIBRATION AND TEST SEQUENCE 

R0410673 A-13 
APPENDIX B PROCESS DATA 

R0410673 B-1 
Appendix B.1 Process and CEMS Data 

R0410673 8-2 
Appendix B.1.1 Sentinel Unit 2 Stratification Test 

R0410673 8-3 Del/at.. ........ , ...... "'--
Data Summary Repor t 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

Source: 

Data Group : 

Report Name : 

Desert Hot Springs, CA 9 2 240 

Turbine 2 

2>1-Min Cales 

~('h~\ Ur'ld 1 s}t<+ TRACE 

Environmental Systems, Inc. 

Start of Report : 

2> I-Min Summary - RATA 

01/30/2013 08,30 End of Report, 01/30/201 3 09,03 validation : All Available Data 

Group#-Channel# 

Long Descrip. 

Short Descrip. 

Units 

Range 

01/30/2013 08:30 

01/30/2013 08:31 

01/30/2013 08:32 

01/30/2013 08:33 

01/30/2013 08:34 

01/30/2013 08;35 

01/30/2013 08:36 

01/30/2013 08 : 37 

01/30/2013 08;38 

01/30/2013 08:39 

01/30/2013 08:40 

01/30/2013 08 : 41 

01/30/2013 08:42 

01/30/2013 08;43 

01/30/2013 08:44 

01/30/2013 08;45 

01/30/2013 08:46 

01/30/2013 08: 4 7 

01/30/2013 08: 4 8 

01/30/2013 08:49 

01/30/ 2013 08:50 

01/30/2013 08:51 

01/30/2013 08 ; 52 

01 /30/2013 08;53 

01/30/2013 08;54 

01/30/2013 08:55 

01/30/2013 08:56 

01/30/ 2013 08:57 

01/30/2013 08:58 

01/30/2013 08:59 

Date/Time Printed: 

G12 -C2 G12-C4 GIZ-CII G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

loS 

loS 

1.6 

1.6 

1.6 

1.6 

1.6 

1.6 

1.6 

1.7 

1.7 

1.7 

1.7 

loB 

1.9 

1.9 

2.0 

2.1 

2.1 

2.1 

2.1 

2.1 

2.2 

2.3 

2.2 

2.3 

2 . 3 

2.3 

2.3 

2.3 

Stk 02 

t 

0-25 

13 .45 

13 . 43 

13 . 42 

13 . 43 

13.43 

13 . 44 

13.42 

13. 43 

13.43 

13. 44 

13.43 

13 . 43 

13.41 

13 .22 

13.03 

13.03 

13 . 04 

13.04 

13.04 

13.05 

13 . 04 

13 . 05 

13.05 

13 . 05 

13.05 

13.04 

13 . 04 

13.05 

13 . 05 

13 . 03 

01/30/2013 10,19 

NOx Mass 

Ib/hr 

0-100 

3 . 57 

3 . 58 

4 . 47 

4.46 

4 .46 

4 . 45 

4 . 46 

4.45 

4.46 

4.45 

4.45 

4.46 

4 .48 

4.48 

4.47 

4.47 

5.36 

5.36 

5.36 

5 . 35 

5 . 36 

5.35 

5.34 

5 . 35 

5.34 

5.3 4 

5.33 

5.33 

5.34 

5.34 

StkFlow 

kscfh 

0-300000 

21789 

21784 

21755 

2174 6 

21736 

21712 

21718 

21696 

21729 

21702 

21707 

21713 

21759 

21226 

20690 

20693 

20699 

20675 

20675 

20681 

20675 

20664 

20646 

2065 9 

20639 

20621 

20586 

2 0614 

2062 4 

20605 

G12-C) GI2-Cl3 GI2-ClO G12-C6 G12-C7 G12-Ca G12 -C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0-1000 

0.1 

0.1 

0.2 

0.2 

0.2 

0.2 

0 . 2 

0.2 

0.2 

0.2 

0.2 

0.2 

1.6 

2.3 

0.3 

0.3 

1.S 

1.B 

1.7 

1.6 

1.S 

1.6 

1.6 

1.6 

1.6 

1.' 

1.3 

1.2 

0.7 

O.B 

CO Mass 

Ib/hr 

0-100 

0.00 

0 . 00 

0.00 

0.00 

0.00 

0 . 00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

2.69 

3 . 58 

0.89 

0.89 

2 . 68 

2.68 

2.68 

2 . 68 

2 . 68 

2.67 

2 . 67 

2.67 

2 . 67 

1. 78 

1. 78 

1. 78 

0 . 89 

0 . 89 

NOx Rate 

Ib/mmBtu 

0-1 

0 . 00 4 

0.004 

0.005 

0.005 

0.005 

0.005 

0.005 

0.005 

0.005 

0 . 005 

0 . 005 

0 . 005 

0.005 

0 . 005 

0.005 

0.005 

0.006 

0.006 

0 . 006 

0 . 006 

0.006 

0.006 

0 . 006 

0 . 006 

0.006 

0.006 

0.006 

0 . 006 

0 . 006 

0.006 

Stk NOXc 

ppm 

0-300 

1.19 

1.18 

1.26 

1.26 

1. 26 

1. 2 7 

1. 26 

1. 26 

1. 26 

1. 34 

1. 34 

1. 34 

1. 34 

1. 38 

1. 42 

1. 42 

1. 50 

1. 58 

1. 58 

1. 58 

1. 58 

1.58 

1. 65 

1. 73 

1. 65 

1. 73 

1. 73 

1. 73 

1. 73 

1. 72 

Stk COe Gas 

ppm 

0-1000 

hscfh 

hscfh 

0-10000 

0.08 

0.08 

0.16 

0.16 

0 . 16 

0.16 

0 . 16 

0 . 16 

0.16 

0.16 

0.16 

0 . 16 

1. 26 

1. 77 

0.22 

0.22 

1.13 

1. 35 

1.28 

1. 20 

1.13 

1.20 

1.20 

1.20 

1.20 

1. 05 

0.98 

0.90 

0.53 

0 . 60 

8 4 92.4 

8513.4 

8513.4 

8498.4 

8494 . 8 

8473.8 

849 9 .0 

8479.2 

8 4 91.8 

8470.2 

8483.4 

8485.8 

8526.6 

8528 . 4 

8518.8 

8520.0 

8511 . 6 

8502 . 0 

8502.0 

8493 . 6 

8502.0 

8486 . 4 

8479 . 2 

84 8 4 . 6 

8476.2 

84 79 . 8 

84 65.4 

8466 . 0 

8470.2 

8 4 84.0 

NlBlnj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

llO . O 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

MW Lo 

0 - 1 

102 

103 

103 . . 

102. 

103. : 

102. ; 

103.1 

103 .. 

102 .. 

102. : 

102. : 

102. : 

103. ; 

103 

103. ! 

103 . ; 

103. ( 

102. ~ 

102 . . 

102. 

103. ( 

102. ! 

103 . ( 

102 .. 

102. : 

102 .. 

102 . 

102. ! 

103. ( 

102 

PagE 
Group#-Channel# G12-C2 G12-C4 G12-C11 G12-C20 G12-C3 G12-C13 G12-C10 G12-C6 G12-C7 G12-C8 G12-C18 G12-C 

Long Descrip. 2>Stk NOx 2>Stk 02 2>NOx Mass 2>StkFlow 2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NIB Inj 2>MW Lo 

Short Descrip . Stk NOx Stk 02 NOx Mass StkFlow Stk CO CO Mass NOx Rat e Stk NOXc Stk COe Gas hsefh NH3Inj MW Lo 

Units ppm % lb/hr ksefh ppm Ib/hr Ib/mmBtu ppm ppm hsefh lb/hr 

Range 0-150 0-25 0-100 0-300000 0-1000 0-100 0-1 0-300 0-1000 0-10000 0-1000 0-1 

01/30/2013 09;00 2.3 13 . 04 5.33 20572 1.1 1. 78 0.006 1. 73 0.83 8459.4 110.0 102 . . 

01/30/2013 09;01 2.4 13.03 6.22 20546 0.8 0.89 0.007 1. 80 0.60 8459.4 110.0 103.1 

01/30/2013 09:02 2.4 13 . 04 6.23 20602 0.7 0.89 0.007 1. 80 0.53 8472 . 0 110.0 102. : 

01/30/2013 09;03 2.4 13.04 6.24 20630 0.6 0.89 0.007 1. 80 0.45 8483.4 110.0 102. : 

Period Average 2.0 13.20 4.96 21076 0.' 1. 29 0.006 1. 50 0.66 8490.2 110.0 102 . 8 

Period Max Value 2.4 13 .45 6.24 21789 2.3 3.58 0 . 007 1. 80 1. 77 8528.4 110.0 103. 

Period Min Value 1.5 13.03 3.57 20546 0.1 0.00 0.004 1.18 0.08 8459.4 110.0 102 . 

Period Totals = 6.6800E+1 4.4864E+2 1. 6849E+2 7.1656E+5 2.9800E+1 4.3700E+1 1.8900E-1 5.0980E+1 2.2590E+1 2.8866E+5 3.7400E+3 3.4963E+ 

Period % Recovery 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100. 

Date/Time Printed: 01/30/2013 10,19 2> I-Min Summary - RATA - Continued PagE 
Appendix B.1.2 Sentinel Unit 2 Ammonia, ROG and NOxlCO Testing 

R0410673 8-4 
Data Summary Report 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 92240 

Source : Turbine 2 

Data Group: 

Report Name : 

~AL \ \jA~t 2 (CMol'r;fitld. 

7 -11,;-r~ -tJ }\.,-so- ! TRACE 

Environmental S./fs/ems, Inc. 

Start of Report: 

2>1-Min Cales 

2>Summary - I-Min RATA 

02/01/2013 14,20 End of Report, 02/01/2013 15,35 validation: All Available Data 

Group#-Channel# 

Long Descrip. 

short Descrip . 

units 

Range 

02/01/2013 14:20 

02/01/2013 14:21 

02/01/2013 14:22 

02/01/2013 14:23 

02/01/2013 14:24 

02/01/2013 14:25 

02/01/2013 14:26 

02/01/2013 14:27 

02/01/2013 14:28 

02/01/2013 14:29 

02/01/2013 14:30 

02/01/2013 14 : 31 

02/01/2013 14:32 

02/01/2013 14:33 

02/01/2013 14:34 

02/01/2013 14:35 

02/01/2013 14:36 

02/01/2013 14:37 

02/01/2013 14:38 

02/01/2013 14;39 

02/01/2013 14:40 

02/01/2013 14:41 

02/01/2013 14:42 

02/01/2013 14:43 

02/01/2013 14:44 

02/01/2013 14:45 

02/01/2013 14:46 

02/01/2013 14:47 

02/01/2013 14:48 

02/01/2013 14:49 

Date/Time Printed: 

G12-C2 G12-C4 Gl2 -ell 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2 . 0 

1.9 

1.8 

1.9 

1.9 

1.9 

1.8 

1.9 

1.9 

1.9 

1.8 

2.2 

1.9 

2.1 

2.2 

2.2 

2.1 

2.0 

2.1 

2.1 

2.0 

2.0 

2.0 

2.0 

1.9 

2.0 

2.1 

2.0 

2.2 

2.2 

Stk 02 

• 

0-25 

14.34 

14.36 

14 . 36 

14.36 

14 . 35 

14.35 

14 . 36 

14.36 

14 .37 

14.36 

14.36 

14.34 

14.37 

14.34 

14 . 34 

14 . 33 

14 .35 

14.34 

14.34 

14.34 

14.35 

14.35 

14.35 

14.35 

14.36 

14 .35 

14.34 

14 . 34 

14.32 

14.32 

02/01/2013 16,13 

NOx Mass 

Ib/hr 

0-100 

3.93 

3.35 

3.36 

3.35 

3.36 

3.35 

3.35 

3.35 

3.36 

3.36 

3.35 

3.91 

3 . 35 

3.91 

3.90 

3.91 

3.91 

3.91 

3.92 

3.93 

3.92 

3.92 

3.92 

3.92 

3.35 

3.92 

3.93 

3.92 

3.93 

3.93 

G12-C20 

2>StkF!ow 

StkFlow 

kscfh 

0-300000 

15572 

15558 

15588 

15561 

15553 

15532 

15542 

15560 

15601 

15586 

15535 

15509 

15541 

15510 

15477 

15489 

15517 

15514 

15558 

15570 

15576 

15546 

15564 

15571 

15556 

15571 

15570 

15554 

15540 

15536 

G12 -C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

G12-CD G12 -ClO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

0.56 

0.56 

0.56 

0.56 

0.56 

0 . 56 

0.56 

0.56 

0 . 56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0 . 56 

0.56 

0.56 

0.56 

0.56 

0 . 00 

0 . 56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.007 

0.006 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.006 

0.007 

0 . 007 

0.007 

0.007 

0.007 

Stk NQXc 

ppm 

0-300 

1. 80 

1. 71 

1. 62 

1. 71 

1. 71 

1. 71 

1. 62 

1. 71 

1. 72 

1. 71 

1. 62 

1. 98 

1.72 

1. 89 

1. 98 

1. 98 

1. 89 

1. 80 

1. 89 

1. 89 

1. 80 

1. 80 

1. 80 

1. 80 

1. 71 

1. 80 

1. 89 

1. 80 

1. 97 

1. 97 

G12-C7 G12-C8 

2>Stk COc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0 .2 7 

0 . 27 

0.27 

0.27 

0 .2 7 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

5344.2 

5323.2 

5333.4 

5324.4 

5329.8 

5322.6 

5317.8 

5323.8 

5329.8 

5332.8 

5315.4 

5322.6 

5309.4 

5323 .2 

5311.8 

5323.8 

5317.2 

5324.4 

5339.4 

5343.6 

5337.6 

5327.4 

5333 .4 

5335.8 

5322.6 

5335.8 

5343 .6 

5338.2 

5349.6 

5348.4 

G12-C18 

2>NH3 Inj 

NH3Inj 

Ib/hr 

0-1000 

106.8 

107.0 

106.7 

107 . 0 

107 . 2 

107.7 

107 .2 

106.5 

106.3 

107.3 

105.7 

104.7 

106.5 

105.2 

104.0 

104.5 

106.0 

107.0 

105 . 7 

106.3 

105.8 

106 . 3 

106 . 7 

106.8 

107.7 

107.0 

106.2 

107.0 

107.0 

106.8 

G12-C 

2>MW Lo 

MW Lo 

0-1 

54. : 

5 4 .. 

54 . . 

54 .. 

54 .. 

54 . . 

54 

54. 

54. : 

54 

54 . . 

5. 

54 .. 

54. : 

54. c 

54. : 

5 •. 

5 •. 

54 .. 

54. 

54 .. 

54. 

55. c 

55. c 

5 4 .. 

55. c 

54. : 

54 

55. c 

55. c 

PagE 
Gro up# -Channel# 

Long Descri p . 

Short Descrip. 

units 

Range 

02/01/2013 14:50 

02/01/2013 14:51 

02/01/2013 14:52 

02/01/2013 14:53 

02/01/2013 14:54 

02/01/2013 14:55 

02/01/2013 14:56 

02/01/2013 14:57 

02/01/2013 14:58 

02/01/2013 14:59 

02/01/2013 15:00 

02/01/2013 15:01 

02/01/2013 15:02 

02/01/2013 15:03 

02/01/2013 15:04 

02/01/2013 15:05 

02/01/2013 15:06 

02/01/2013 15:07 

02/01/2013 15:08 

02/01/2013 15:09 

02/01/2013 15:10 

02/01/2013 15:11 

02/01/2013 15:12 

02/01/2013 15:13 

02/01/2013 15:14 

02/01/2013 15:15 

02/01/2013 15:16 

02/01/2013 15:17 

02/01/2013 15:18 

02/01/2013 15:19 

02/01/2013 15:20 

02/01/2013 15:21 

02/01/2013 15:22 

02/01/2013 15;23 

02/01/2013 15;24 

02/01/2013 15:25 

02/01/2013 15:26 

02/01/2013 15;27 

02/01/2013 15:28 

02/01/2013 15:29 

Date/Time Printed: 

G12 - C2 G12-C4 G12 - C11 

2::>Stk NOx 

Stk NOx 

ppm 

0-150 

2::>Stk 02 2::>NOx Mass 

2.1 

2.1 

2.2 

2.1 

1.9 

2 . 1 

2.1 

2.1 

2.2 

2.1 

2.2 

2.1 

2.1 

2.1 

2.0 

2.0 

2.0 

2.0 

2 . 2 

2.2 

2.1 

2.1 

2.1 

2.2 

2.0 

2.1 

2.2 

2.0 

2.1 

2.1 

2.2 

2.2 

2.2 

2.2 

2.1 

2.0 

2.1 

2.1 

2.1 

2.2 

Stk 02 

t 

0-25 

14.33 

14.33 

14.33 

14.34 

14.35 

14.33 

14.32 

14.32 

14.32 

14.33 

14.32 

14.32 

14 .31 

14 .33 

14.33 

14.34 

14.34 

14.34 

14.32 

14.33 

14 .33 

14.34 

14 . 33 

14.30 

14.31 

14.32 

14 .32 

14.34 

14.31 

14.32 

14.31 

14 . 31 

14.31 

14.31 

14 .32 

14.32 

14.30 

14.31 

14.31 

14.31 

02/01/2013 16,13 

NOx Mass 

lb/hr 

0 - 100 

3.94 

3.94 

3.94 

3.94 

3.38 

3.95 

3.94 

3.95 

3.94 

3.94 

3.94 

3.94 

3.95 

3.94 

3.94 

3.94 

3.93 

3.92 

3.94 

3.94 

3.93 

3.93 

3.94 

3.95 

3.96 

3.95 

3.97 

3.96 

3.98 

3.98 

3.99 

3.98 

3.98 

3.98 

3.98 

3.97 

3.98 

3.98 

3.98 

3.99 

G12-C20 

2::>StkFlow 

StkFlow 

kscfh 

0-300000 

15586 

15586 

15579 

15605 

15637 

15625 

15582 

15620 

15585 

15600 

15568 

15577 

15596 

15583 

15595 

15605 

15596 

15554 

15580 

15590 

15569 

15584 

15586 

15564 

15617 

15601 

15688 

15689 

15697 

15711 

15725 

15703 

15711 

15722 

15723 

15707 

15689 

15694 

15722 

15736 

G12-C3 

2::>Stk CO 

Stk CO 

ppm 

0-1000 

0.3 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0 .3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.3 

0.2 

0.2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

G12 - Cl3 G12-CI0 G12-C6 

2::>CO Mass 2::>NOx Rate 2::>Stk NOXe 

CO Mass 

lb/hr 

0 - 100 

0.56 

0.56 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.57 

0.56 

0.00 

0.00 

0.57 

0.00 

0.00 

0.00 

0.00 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.006 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0 - 300 

1. 89 

1. 89 

1. 98 

1. 89 

1. 71 

1. 89 

1. 88 

1. 88 

1. 97 

1. 89 

1. 97 

1. 88 

1. 88 

1. 89 

1. 80 

1. 80 

1. 80 

1. 80 

1. 97 

1. 98 

1. 89 

1. 89 

1. 89 

1. 97 

1. 79 

1. 88 

1. 97 

1. 80 

1. 88 

1. 88 

1. 97 

1. 97 

1. 97 

1. 97 

1. 88 

1. 79 

1. 88 

1. 88 

1. 88 

1. 97 

G12-C7 G12-C8 

2::>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hscfh 

0-1000 0 - 10000 

0.27 

0.27 

0.18 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0.27 

0.18 

0 . 18 

0.18 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

5357.4 

5357.4 

5355.0 

5355.6 

5358.6 

5370.6 

5364.0 

5377.2 

5365.2 

5362.2 

5359.2 

5362.2 

5377.2 

5356.2 

5360.4 

5355.6 

5352.6 

5338.2 

5363.4 

5358.6 

5351.4 

5348.4 

5357.4 

5374.2 

5384.4 

5370.6 

5400.6 

5384.4 

5412.0 

5408.4 

5421.6 

5413.8 

5416.8 

5420.4 

5412.6 

5407.2 

5417.4 

5410.8 

5420.4 

5425.2 

G12-C18 

2::>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

105.2 

105.8 

105.7 

107.3 

107.3 

106.0 

106.5 

106.3 

106.7 

106.7 

106.8 

106.8 

107.2 

107.5 

107.5 

106.8 

107.2 

106.2 

105.7 

105.8 

107.2 

104.3 

106.0 

107.0 

106.7 

107.2 

107.3 

109.0 

108.8 

107.8 

107.5 

108.2 

107.8 

108.8 

108.3 

108.3 

108.7 

107.8 

106.8 

107.8 

2>Summary - l-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

55. ! 

S5.1 

54. : 

55.1 

54 

55.1 

55 

55 . . 

55. 

55. 1 

54. 

55 .. 

55.: 

54. : 

55 .. 

54 

55.1 

54. : 

55 . . 

55.1 

54. : 

55.1 

55.: 

55 . . 

55 ' 

55 . . 

55. 

55. 

56.1 

55 .. 

56. : 

56.1 

S5. < 

56. 1 

56.1 

55 . . 

55. : 

56.1 

56 .. 

55. 

PagE 
Group#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

02/01/2013 15:30 

02/01/2013 15:31 

02/01/2013 15:32 

02/01/2013 15:33 

02/01/2013 15:34 

02/01/2013 15:35 

Period Average 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12 - C2 G12-C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.1 

2.0 

2.1 

2.1 

2.0 

2.0 

2.1 

2.2 

1.8 

1 . 5660E+2 

100.0 

Stk 02 

• 

0-25 

14.3 2 

14.32 

14.32 

14 .33 

14 . 32 

14.32 

14 . 33 

14.37 

14 .30 

1.0892E+3 

100.0 

02/01/2013 16,13 

NOx Mass 

1b/hr 

0 - 100 

3.98 

3.97 

3.98 

3.96 

3.97 

3.97 

3.84 

3.99 

3.35 

StkFlow 

kscfh 

0-300000 

15726 

15681 

15733 

15658 

15678 

15674 

15604 

15736 

15477 

2.9221E+2 1.1858E+6 

100.0 100.0 

G12-C3 G12 - Cl3 G12-C10 G12 - C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0 - 1000 

0.2 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0 .3 

0.2 

2.1700E+l 

100.0 

CO Mass 

Ib/hr 

0-100 

0.00 

0.57 

0.00 

0.57 

0.57 

0.57 

0.48 

0.57 

0.00 

3.6530E+1 

100.0 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.006 

S.1900E-1 

100.0 

stk NOXc 

ppm 

0 - 300 

1. 88 

1. 79 

1. 88 

1. 89 

1. 79 

1. 79 

1. 85 

1. 98 

1. 62 

1.4066E+2 

100.0 

Stk COc Gas hscfh 

ppm 

0-1000 

0.18 

0 .2 7 

0.18 

0.27 

0.27 

0.27 

0.26 

0 .2 7 

0.18 

1.9530E+1 

100.0 

hscfh 

0 - 10000 

5413 .8 

5398.2 

5416.2 

5382.0 

5397.0 

5395.8 

5361.2 

5425.2 

5309.4 

4.0745E+S 

100.0 

NH3Inj 

Ib/hr 

0-1000 

109.3 

108.5 

108.5 

107.3 

108.5 

108.0 

106 . 9 

109. 3 

104.0 

MW Lo 

0-1 

55. 

55.: 

55.: 

55.· 

55. · 

55.· 

55 . 1 

56. 

54. 

8.1250E+3 4.1874E+ 

100.0 100. 

2>Summary - I-Min RATA - Continued PagE 
Data Summary Report 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 92240 

Source : Turbine 2 

Data Group : 2>1-Min Cales 

Report Name : 

~~\ 0...: r- Z (j,NlVrttcllc.(. TRACE ~-l \71"lL- ~~-S7-2- EnIJironmen/al Systems, [nc. 

Start of Report: 

2>Summary - I-Min RATA 

02/01/2013 15,53 End of Report, 02/01/2013 17,09 validation: All Available Data 

Group#-Channel# 

Long Descrip . 

Short Descri p. 

Units 

Range 

02/01/2013 15:53 

02/01/2013 15 : 54 

02/01/2013 15:55 

02/01/2013 15:56 

02/01/2013 15:57 

02/01/2013 15:58 

02/01/2013 15:59 

02/01/2013 16:00 

02/01/2013 16:01 

02/01/2013 16:02 

02/01/2013 16:03 

02/01/2013 16:04 

02/01/2013 16:05 

02/01/2013 16:06 

02/01/2013 16:07 

02/01/2013 16:08 

02/01/2013 16:09 

0 2 /01/2013 16:10 

02/01/2013 16:11 

02/01/2013 16:12 

02/01/2013 16:13 

02/01/2013 16:14 

02/01/2013 1 6 :15 

02/01/2013 16:16 

02/01/2013 16:17 

02/01/2013 16:18 

02/01/2013 16:19 

02/01/2013 16:20 

02/01/2013 16:21 

02/01/2013 16:22 

Date/Time Printed: 

G12-C2 G12-C4 GI2-CII 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.3 

2 . 0 

2.2 

2.1 

2.0 

2.1 

2.1 

2.1 

2.2 

2.2 

2.3 

2.3 

2.1 

2.1 

2.1 

2 . 2 

2.2 

2.3 

2.2 

2 . 1 

2.2 

2.1 

2.2 

2.2 

2.2 

2.2 

2.2 

2.0 

2.1 

2.1 

Stk 02 

• 

0-25 

14 . 31 

14.31 

14.31 

1 4. 34 

14.34 

14.34 

14.35 

14.34 

14.33 

14.32 

14.3 2 

14.32 

14.34 

14.34 

14.34 

14.30 

14.32 

14.33 

14 . 32 

14 . 32 

14.31 

14 . 31 

14 . 29 

14 . 29 

1 4. 30 

1 4 .28 

14 . 29 

14.31 

14 . 30 

14 . 31 

02/01/2013 17,53 

NOx Mass 

Ib/hr 

0-100 

4.52 

3.95 

3 . 96 

3.93 

3.92 

3.92 

3.92 

3.93 

3 . 93 

3.94 

4.51 

4.51 

3.93 

3.93 

3.93 

3.94 

3.94 

4.51 

3.96 

3.96 

3.96 

3.97 

3.98 

3.99 

3 . 98 

3.99 

3.98 

3.99 

4.00 

3.99 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

15612 

15603 

15647 

15586 

15559 

155 4 9 

15560 

15561 

15564 

15580 

15584 

15587 

15586 

15586 

15586 

15529 

15566 

15621 

15650 

15655 

15635 

15678 

15648 

15718 

15682 

15671 

15660 

15739 

15747 

15741 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0 -1 000 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.3 

0 . 3 

0.3 

0 . 3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.2 

0.2 

0.2 

0.3 

0. 2 

0.3 

0.3 

0 . 3 

0.3 

0.3 

0.3 

0.3 

GI2 - C13 G12 -Cla G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

co Mass 

Ib/hr 

0 - 100 

0.57 

0.56 

0.57 

0.56 

0.00 

0.00 

0 . 56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.56 

0 . 00 

0 . 00 

0 . 00 

0.57 

0 . 00 

0.57 

0.57 

0.57 

0 . 57 

0 . 57 

0.57 

0.57 

NOx Rate 

Ib/mmBtu 

0 - 1 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

0 . 007 

0.008 

0.008 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.008 

0 . 007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

2.06 

1. 79 

1. 97 

1. 89 

1. 80 

1. 89 

1. 89 

1. 89 

1. 98 

1. 97 

2.06 

2.06 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

2.07 

1. 97 

1. 88 

1. 97 

1. 88 

1. 96 

1. 96 

1. 97 

1.96 

1.96 

1. 79 

1. 88 

1. 88 

G12-C7 G12-C8 GI2-CIa 

2 >Stk COe 2 >Gas Flow 2 >NH3 Inj 

Stk COe Gas hscfh NH3 Inj 

ppm 

0-1000 

0.27 

0. 2 7 

0.27 

0.27 

0 . 18 

0.18 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0.27 

0 . 18 

0.27 

0.18 

0 . 18 

0.18 

0.27 

0.18 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

hscfh 

0-10000 

5382.6 

5379.6 

5394.6 

5349.0 

5340.0 

5336.4 

5332.2 

5340.6 

534 9 .6 

5363.4 

5364.6 

5365 . 8 

5349.0 

5349.0 

5349.0 

5362.2 

5358 . 6 

5369.4 

5387.4 

5389 . 2 

5390.4 

5405.4 

5411.4 

5435 . 4 

5415.0 

5427.6 

5415.6 

5426.4 

5 437.2 

5427.0 

Ib/hr 

0-1000 

106.7 

106.3 

105.8 

106.3 

106.8 

105.7 

106.0 

105.3 

105.3 

105.3 

106.2 

105.5 

106.3 

106.3 

106.3 

105.3 

106 . 5 

106.3 

108.3 

108.7 

108.7 

108.3 

108.0 

108.7 

109 . 7 

108.8 

108.7 

108 . 5 

107.5 

107.8 

G12-C 

2>MW La 

MW La 

0 - 1 

55 . . 

55 .. 

55.! 

54. : 

54 . . 

54. : 

54. 

54 

54 

55. < 

55 

55 .. 

55.: 

55.: 

55.: 

55. : 

54 

55 .. 

55. 

55.! 

56.1 

55. : 

55. ! 

56. : 

55. : 

56. : 

56 . : 

56. : 

56.: 

56. : 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descrip. 

Units 

Range 

02/01/2013 16:23 

02/01/2013 16:24 

02/01/2013 16:25 

02/01/2013 16:26 

02/01/2013 16:27 

02/01/2013 16:28 

02/01/2013 16:29 

02/01/2013 16:30 

02/01/2013 16:31 

02/01/2013 16:32 

02/01/2013 16:33 

02/01/2013 16:34 

02/01/2013 16:35 

02/01/2013 16:36 

02/01/2013 16:37 

02/01/2013 16:38 

02/01/2013 16:39 

02/01/2013 16:40 

02/01/2013 16:41 

02/01/2013 16:42 

02/01/2013 16;43 

02/01/2013 16:44 

02/01/2013 16:45 

02/01/2013 16;46 

02/01/2013 16;47 

02/01/2013 16:48 

02/01/2013 16:49 

02/01/2013 16:50 

02/01/2013 16:51 

02/01/2013 16;52 

02/01/2013 16:53 

02/01/2013 16:54 

02/01/2013 16:55 

02/01/2013 16;56 

02/01/2013 16:57 

02/01/2013 16:58 

02/01/2013 16:59 

02/01/2013 17;00 

02/01/2013 17;01 

02/01/2013 17:02 

Date/Time Printed: 

G12-C2 G1 2 -C4 G12-ell 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.0 

2.1 

2.1 

2.1 

2.1 

2.1 

2.0 

2.1 

2.2 

2.1 

2.2 

2.2 

2.1 

2.0 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

2.2 

2.1 

2.2 

2.2 

2.2 

2.1 

2.0 

2.0 

2.0 

2.1 

2.0 

2.0 

2.1 

2.1 

2.2 

2.2 

2.1 

2.1 

2.2 

Stk 02 

, 

0-25 

14.32 

14.31 

14.32 

14.30 

14.30 

14.32 

14.32 

14.30 

14.29 

14.31 

14.31 

14.30 

14.32 

14.33 

14.33 

14.32 

14.33 

14.31 

14.32 

14.31 

14.30 

14.31 

14.31 

14 .30 

14.29 

14.30 

14 .32 

14 .32 

14.34 

14.33 

14.32 

14.33 

14.32 

14.34 

14.34 

14.32 

14 . 33 

1 4.34 

1 4. 33 

14.33 

02/01/2013 17,53 

NOx Mass 

lb/br 

0-100 

3.98 

3.99 

3.98 

3.98 

3.99 

3.97 

3.96 

3.98 

3.99 

3.98 

3.99 

3.99 

3.97 

3.96 

3.95 

3.97 

3.95 

3.98 

3.97 

3.98 

3.98 

3.99 

3.99 

4.00 

4.01 

4.00 

3.98 

3.97 

3.95 

3.95 

3.95 

3.94 

3.94 

3.92 

3.93 

3.94 

3 .93 

3.94 

3.95 

3.95 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

15737 

15748 

15735 

15694 

15703 

15704 

15657 

15684 

15691 

15704 

15727 

15731 

15674 

15674 

15647 

15693 

15625 

15696 

15704 

15708 

15698 

15746 

15730 

15748 

15761 

1 5774 

15747 

15700 

15661 

15633 

15610 

15592 

1 5564 

15535 

15572 

15585 

15560 

15628 

15616 

15633 

G12 -C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.3 

0.2 

0.2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0 .3 

0.3 

0.3 

0.3 

0.3 

0 .3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

G12-Cl3 G12-CIO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

lb/br 

0-100 

0.57 

0.00 

0.00 

0.00 

0.00 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.56 

0.57 

0.56 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.00 

0.00 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 79 

1. 88 

1. 88 

1. 88 

1. 88 

1. 88 

1. 79 

1. 88 

1.96 

1. 88 

1. 97 

1. 97 

1. 88 

1. 80 

1.89 

1. 88 

1. 89 

1. 88 

1. 88 

1. 88 

1. 88 

1. 97 

1. 88 

1. 97 

1.96 

1. 97 

1. 88 

1. 79 

1. 80 

1. 80 

1. 88 

1. 80 

1. 79 

1. 89 

1. 89 

1. 97 

1. 98 

1. 89 

1. 89 

1. 98 

G12-C7 G12-CS 

2>Stk CDc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

0.27 

0.18 

0.18 

0.18 

0 . 18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

o 27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0.18 

0.27 

0.27 

0.27 

0 .27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

5417.4 

5429.4 

5416.8 

5419.2 

5422.2 

5406.0 

5389.8 

5415.6 

5426.4 

5414.4 

5422.2 

5431.8 

5395.8 

5387.4 

5378.4 

5402.4 

5370.6 

5411.4 

5406.0 

5415.6 

5420.4 

5428.8 

5423.4 

5437.8 

5450.4 

5446.8 

5421.0 

5404.8 

5374.8 

5373.6 

5373.6 

5359.2 

5358.0 

5331.6 

5344.2 

5365.2 

5348.4 

5363.4 

5367.6 

5373.6 

GI2 -CIS 

2>NH3 Inj 

NH3Inj 

lb/br 

0-1000 

108.3 

108.3 

108.7 

109.2 

108.7 

108.7 

107.5 

108.3 

109.3 

108.3 

106.0 

109.2 

108.7 

107.2 

108.0 

106.0 

107.2 

107.8 

107.8 

107.0 

107.8 

106.7 

107.5 

107.3 

107.0 

108.8 

109.7 

108.2 

106.8 

105.5 

107.2 

107.5 

1 07.2 

105.0 

104.8 

105.3 

104.8 

103.8 

105.0 

105.2 

2>Summary - 1-Min RATA - Continued 

G12-C 

2>MW La 

MW La 

0-1 

56.1 

56. : 

56. : 

56.1 

56. ! 

56 . ! 

55. ! 

56 .. 

56.1 

56.1 

56. : 

56.! 

55 .. 

55 .. 

55 .. 

55. 

55 .. 

56.1 

55. 

56. : 

56.1 

56. : 

56. : 

56 .. 

56.: 

56.: 

56.1 

56.1 

55. : 

55 .. 

55 . . 

55. 

55 .. 

54. ; 

55.1 

55 .. 

55.1 

55. ! 

55. : 

55. ! 

Pag~ 
Group#-Channel# 

Long Descrip . 

Short Descrip. 

Units 

Range 

02/01/2013 17 : 03 

02/01/2013 17:04 

02/01/2013 17:05 

02/01/2013 17:06 

02/01/2013 17:07 

02/01/2013 17 : 08 

02/01/2013 17:09 

Period Average = 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

2 . 1 

2.1 

2 . 3 

2.0 

1. 6360E+2 

100.0 

G12 -C4 G12-C11 

2>Stk 02 2>NOx Mass 

Stk 02 

, 

0 -2 5 

NOx Mass 

lb/hr 

0-100 

14.31 3 . 97 

14.32 3.97 

14 . 32 3.96 

14 . 31 3.9S 

14 . 32 3.95 

14.32 3.96 

14.33 3.96 

14.32 3.99 

14.35 4.52 

14.28 3.92 

1 . 1024E+3 3.0731E+2 

100.0 100.0 

02/01/2013 17,53 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

15668 

15695 

15636 

15605 

15617 

15639 

15681 

15653 

15774 

15529 

1.2052E+6 

100.0 

G12 - C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.2 

0.2 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0 .2 

2.1400E+1 

100.0 

G12 - C13 G12 - C10 G12-C6 

2>CO Ma ss 2>NOx Rate 2>Stk NOXc 

CO Mass 

1b/hr 

0-100 

0.00 

0 . 00 

0 . 57 

0.00 

0 . 56 

0.57 

0.57 

0.44 

0.57 

0.00 

3.3920E+1 

100.0 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

5.4300E-1 

100 . 0 

Stk NOXc 

ppm 

0-300 

1. 88 

1. 88 

1. 88 

1. 88 

1. 88 

1. 88 

1. 89 

1. 90 

2.07 

1. 79 

1.4664E+2 

100.0 

G12-C7 G12-C8 

2>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hscfh 

0-1000 0-10000 

0.18 

0.18 

0.27 

0.18 

0.27 

0.27 

0.27 

0.25 

0.27 

0.18 

1.9260E+1 

100.0 

5401.8 

5403.0 

5382.6 

5380.2 

5376.0 

5383.8 

5389.8 

5390.5 

5450.4 

5331.6 

4.1506E+5 

100.0 

G12-C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

106 .2 

106.8 

106.8 

106 . 8 

105 .7 

106.5 

105.2 

107.1 

109.7 

103.8 

8.24S2E+3 

100.0 

2>Summary - I - Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

56.1 

56.1 

5S. : 

55. ! 

55. : 

S5. ! 

S5. : 

55.6 

56. 

54. 

4.2831E+ 

100. 

PagE 
Data Summary Report 

Company: CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 

Source : 

Data Group: 

Report Name: 

Start of Report: 

Turbine 2 

2>1-Min Cales 

2>Summary - I-Min RATA 

02/01/2013 09,10 

G12-C4 

~11'\l\ VII;} l 

92240 :J-dS'TIL-- N\-\';-t~ - ( 

End of Report, 02/01/2013 10,3 4 

G12-ell Gl2 -Cl3 

tONlt \ 'If#-t TRACE 

Ellvirollmellial Syslems, Illc. 

Validation: All Available Data 

Group#-Channel# G12 -ClO G12-C6 G12-C7 G12-CB G12 -C1S 

Long Descrip. 

Short Descrip. 

units 

G12-C2 

2>Stk NOx 

Stk NOx 

2 >Stk 02 2 >NOx Mass 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

G12-C3 

2>Stk CD 

Stk CO 

ppm 

0-1000 

2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk CDc 2>Gas Flow 2>NH3 Inj 

G12-C 

2>MW La 

MW La 

Range 

02/01/2013 09:10 

02/01/2013 09:11 

02/01/2013 09 : 12 

02/01/2013 09:13 

02/01/2013 09:14 

02/01/2013 09 : 15 

02/01/2013 09:16 

02/01/2013 09:17 

02/01/2013 09:18 

02/01/2013 09:19 

02/01/2013 09:20 

02/01/2013 09:21 

02/01/2013 09:22 

02/01/2013 09:23 

02/01/2013 09:24 

02/01/2013 09:25 

02/01/2013 09:26 

02/01/2013 09:27 

02/01/2013 09:28 

02/01/2013 09:29 

02/01/2013 09:30 

02/01/2013 09:31 

02/01/2013 09:32 

0 2 /01/2013 09:33 

02/01/2013 09:34 

02/01/2013 09:35 

02/01/2013 09:36 

02/01/2013 09:37 

02/01/2013 09:38 

02/01/2013 09:39 

Date/Time Printed: 

ppm 

0-150 

2 . 6 

2.5 

2 .6 

2.4 

2.4 

2.4 

2.5 

2.5 

2.5 

2.5 

2.5 

2.6 

2.5 

2.5 

2.5 

2.6 

2.5 

2.6 

2.6 

2 . 5 

2.4 

2.4 

2.4 

2.4 

2 .4 

2.5 

2.5 

2.5 

2.5 

2.5 

Stk 02 

• 

0-25 

13 .41 

13 .4 1 

13 .4 0 

13.41 

13.41 

13.41 

13.41 

13 .42 

13 .42 

13 .40 

13 .41 

13 . 40 

13 .40 

13.40 

13.40 

13.41 

13 .41 

13 .40 

13 .41 

13 .41 

13 .40 

13 .42 

13 .41 

13 .41 

13 .4 1 

13. 4 1 

13.40 

13 .4 1 

13.41 

13 .41 

02/01/2013 16,12 

NOx Mass 

Ib/hr 

0-100 

5.81 

5.08 

5.82 

5.09 

5 . 09 

5.08 

5.07 

5.07 

5.07 

5.08 

5 . 06 

5.80 

5.08 

5.08 

5.08 

5.79 

5.06 

5.82 

5.81 

5 . 06 

5.08 

5.06 

5.07 

5 . 06 

5.06 

5.07 

5.09 

5.09 

5.09 

5.08 

17661 

17651 

17655 

17671 

17674 

17636 

17592 

17634 

17638 

17605 

17581 

17602 

17626 

17625 

17609 

17589 

17579 

17654 

17647 

17582 

17628 

17584 

17593 

17556 

17572 

17592 

17655 

17664 

17664 

17627 

0 . 7 

0 . 7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.8 

0.7 

0.7 

0.8 

0.7 

0 . 7 

0 . 7 

0.6 

0.6 

0.6 

0.6 

0.6 

0.6 

0.7 

0 . 7 

0.7 

0.7 

0.7 

0.7 

0.6 

0.6 

0.6 

0.6 

CO Mass 

1b/hr 

0-100 

0 . 73 

0 . 73 

0.73 

0.73 

0.73 

0.73 

0 . 72 

0 . 72 

0.72 

0.73 

0.72 

0.73 

0.73 

0 .7 3 

0.73 

0.72 

0 . 72 

0.73 

0.73 

0.72 

0.73 

0.72 

0.72 

0.72 

0 . 7 2 

0.72 

0.73 

0.73 

0.73 

0 . 73 

NDx Rate 

Ib/mmBtu 

0-1 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.008 

0.007 

0.008 

0 . 008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

Stk NDXc 

ppm 

0-300 

2.05 

1. 97 

2.05 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

2.05 

1. 97 

1. 97 

1. 97 

2.05 

1. 97 

2 . 05 

2.05 

1. 97 

1. 89 

1. 89 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

Stk CDc Gas hscfh NH3Inj 

ppm 

0-1000 

0 . 55 

0 . 55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.63 

0.55 

0.55 

0.63 

0.55 

0.55 

0.55 

0.47 

0.47 

0.47 

0.47 

0.47 

0.47 

0 . 55 

0 . 55 

0.55 

0.55 

0 . 55 

0.55 

0.47 

0 .4 7 

0.47 

0.47 

hscfh 

0-10000 

6920.4 

6916.8 

6927.6 

6924.6 

6925.8 

6910.8 

6893.4 

6900.6 

6902.4 

6907.8 

6889.2 

6906.6 

6916.2 

6915.6 

6909.6 

6892.2 

6888.6 

6927.0 

6915.0 

6889.8 

6916.8 

6881.4 

6894.0 

6879.6 

6885 . 6 

6893.4 

6927.6 

6921.6 

6921.6 

6907.2 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1 10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

0-1 

80 . ~ 

80. : 

80. : 

80. : 

80 . . 

80 . . 

79. ' 

80.1 

80. : 

80. ( 

79. 

79. ' 

79. 

80. : 

79 . ~ 

80 . 1 

79. ' 

79. : 

80.1 

79 . ~ 

80,1 

79. ' 

79. 

79 

79. ' 

79. 

80 . . 

79. : 

79. : 

79. : 

Pag( 
Group#-Channel# 

Long Descrip . 

Short Descrip . 

Units 

Range 

02/01/2013 09:40 

02/01/2013 09:41 

02/01/2013 09:42 

02/01/2013 09:43 

02/01/2013 09:44 

02/01/2013 09:45 

02/01/2013 09:46 

02/01/2013 09:47 

02/01/2013 09:48 

02/01/2013 09:49 

02/01/2013 09:50 

02/01/2013 09:51 

02/01/2013 09:52 

02/01/2013 09:53 

02/01 / 2013 09:54 

02/01/2013 09:55 

02/01/2013 09:56 

02/01/2013 09:57 

02/01/2013 09:58 

02/01/2013 09:59 

02/01/2013 10:00 

02/01/2013 10:01 

02/01/2013 10:02 

02/01/2013 10:03 

02/01/2013 10:04 

02/01/2013 10:05 

02/01/2013 10:06 

02/01/2013 10:07 

02/01/2013 10:08 

02/01/2013 10:09 

02/01/2013 10:10 

02/01/2013 10:11 

02/01/2013 10:12 

02/01/2013 10:13 

02/01/2013 10:14 

02/01/2013 10:15 

02/01/2013 10:16 

02/01/2013 10:17 

02/01/2013 10:18 

02/01/2013 10:19 

Date/Time Printed: 

G12 -C2 G12 -C4 G12-Cl1 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.S 

2.4 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.S 

2.S 

2.6 

2.6 

2.6 

2. 4 

2.S 

2.S 

2.6 

2.6 

2.4 

2.4 

2.S 

2.S 

2.S 

2.4 

2.4 

2.S 

2.S 

2.4 

2.4 

2.4 

2.4 

2.4 

2.S 

2.6 

2.4 

2.4 

2.S 

2.4 

2.4 

Stk 02 

• 

0 - 25 

13.40 

13.41 

13 .41 

13 .41 

13 .40 

13 .40 

13 .4 0 

13.39 

13.39 

13.40 

13. 4 0 

13.39 

13.39 

13 .40 

13.42 

13 .41 

13.40 

13.39 

13 .39 

13 .39 

13 .40 

13 .41 

13 .40 

13 .41 

13 .42 

13.42 

13.41 

13.40 

13.40 

13.41 

13.41 

13 .42 

13.41 

13 .4 1 

13.40 

13 .41 

13 .41 

13 .40 

13 .41 

13. 43 

02/01/2013 16,12 

NOx Mass 

1b/hr 

0-100 

5.08 

5.06 

5.80 

5.80 

5.80 

5.81 

5.82 

5.80 

5.81 

5.08 

5.08 

5.81 

5.82 

5.84 

5.09 

5.10 

5.11 

5.84 

5.85 

5.10 

5.09 

5.10 

5.09 

5.09 

5.09 

5.10 

5.11 

5.11 

5.11 

5.10 

5.10 

5.08 

5.08 

5.07 

5.80 

5.08 

5.09 

5.10 

5.09 

5.08 

StkFlow 

ksefh 

0 - 300000 

17616 

17561 

17621 

17621 

17602 

17614 

17646 

17578 

17598 

17600 

17611 

17615 

17641 

17712 

17683 

17722 

17727 

17704 

17728 

17650 

17651 

17693 

17664 

17668 

17692 

17716 

17726 

17730 

17710 

17716 

17696 

17650 

17625 

17598 

17603 

17622 

17667 

17674 

17657 

17682 

G12-C3 G12 -C13 G12 -CIa G12-C6 G12 -C7 G12 -CS G12 -CIS G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0-1000 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.6 

0 . 6 

0.6 

0.6 

0.6 

0.6 

0.6 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.6 

O.S 

0.6 

0.7 

0.6 

0.6 

0.7 

0.7 

0.7 

0.6 

0.6 

0.8 

0.7 

0.6 

0.7 

0.7 

0.7 

0.6 

CO Mass 

Ib/hr 

0-100 

0.73 

0 .72 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0 . 73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.72 

0.73 

0.73 

0.73 

0.73 

0 . 73 

0.73 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.007 

0.008 

0.008 

0.008 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 .007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1. 97 

1. 89 

2.05 

2.05 

2.05 

2.05 

2.05 

2.12 

2.04 

1. 97 

1. 97 

2.04 

2.04 

2.05 

1. 89 

1. 97 

1. 97 

2.04 

2.04 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 89 

1. 89 

1. 97 

1. 97 

1. 89 

1. 89 

1. 89 

1. 89 

1. 89 

1. 97 

2.05 

1. 89 

1. 89 

1. 97 

1. 89 

1. 90 

Stk COe Gas 

ppm 

hsefh 

hsefh 

0-1000 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0 . 55 

0 .47 

0.47 

0.47 

0.47 

0.47 

0.47 

0.47 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.47 

0.39 

0.47 

0.55 

0.47 

0 .47 

0.55 

0.55 

0.55 

0.47 

0.47 

0.63 

0.55 

0.47 

0.55 

0.55 

0 . 55 

0.47 

0-10000 

6912.0 

6881.4 

6904.8 

6904.8 

6906.6 

6911.4 

6924. a 

6906.6 

6914.4 

6906.0 

6910 . 2 

6921.0 

6931.2 

6949.8 

6919.8 

6944.4 

6955.8 

6955.8 

6965.4 

6934.8 

6925.8 

6933.0 

6931. 2 

6923.4 

6923.4 

6933. a 

6946.2 

6957.0 

6949.2 

6942.0 

6934.2 

6907.2 

6906.6 

6895.8 

6907.2 

6905.4 

6922.8 

6934.8 

6919.2 

6910.2 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110. a 

110. a 

110.0 

110 .0 

1 10.0 

110. a 

110.0 

110. a 

110.0 

110.0 

110.0 

110.0 

110. a 

110.0 

llO.O 

110.0 

110.0 

110.0 

llO. a 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110. a 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

MW Lo 

0-1 

80.1 

79 . 

79. : 

79. : 

79.: 

79. ! 

79. : 

80 .1 

79. 

79 .. 

80 

80.1 

80 .: 

80.: 

80 .1 

80. : 

80. : 

80. 

80. 

80. ! 

80 . 1 

80. 

79 . 

80 . 1 

80 .: 

80 .: 

80 

80. 

80 

80 .. 

80.: 

80.1 

80 .1 

79 .. 

80 

79. 

79. : 

79. 

79. 

79 .. 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descrip . 

units 

Range 

02/01/2013 10:20 

02/01/2013 10:21 

02/01/2013 10:22 

02/01/2013 10:23 

02/01/2013 10:24 

02/01/2013 10:25 

02/01/2013 10:26 

02/01/2013 10:27 

02/01/2013 10:28 

02/01/2013 10:29 

02/01/2013 10:30 

02/01/2013 10:31 

02/01/2013 10:32 

02/01/2013 10 : 33 

02/01/2013 10:34 

Period Average = 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12-C2 

2>Stk NDx 

Stk NDx 

ppm 

0-150 

2.5 

2.5 

2.4 

2.4 

2.4 

2.4 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2 . 5 

G1 2 -C4 G12-Cll G12-C20 

2>Stk 02 2>NOx Mass 2>StkFlow 

Stk 02 

• 

0-25 

13.42 

13 .39 

13 .41 

13 .41 

13 .42 

13 . 41 

13 .4 3 

13 .43 

13 . 4 3 

13.43 

13 . 42 

13 .4 1 

13.42 

13.42 

13 . 42 

NOx Mass 

lb/hr 

0-100 

5.09 

5.09 

5.07 

5.07 

5 . 05 

5.06 

5 . 04 

5 . 05 

5.05 

5 . 06 

5 . 06 

5.06 

5.07 

5 . 06 

5.07 

StkFlow 

kscfh 

0-300000 

17698 

17613 

17612 

17596 

17571 

17569 

17559 

17573 

17574 

17599 

17606 

17579 

17621 

17600 

17635 

G12-C3 G12-C13 G12-C10 G1 2 -C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk CDc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0-1000 

0.7 

0.6 

0.6 

0.6 

0.6 

0.7 

0 . 6 

0.6 

0.6 

0.6 

0.5 

0.5 

0.6 

0.6 

0 . 6 

CD Mass 

1b/hr 

0-100 

0.73 

0.73 

0 . 72 

0 . 72 

0 .72 

0.72 

0.72 

0.72 

0.72 

0.72 

0 . 72 

0.72 

0.72 

0 . 72 

0 . 72 

NOx Rate 

lb/mmBtu 

0 - 1 

0.007 

0 . 007 

0.007 

0 . 007 

0 . 007 

0 . 007 

0 . 007 

0 . 007 

0.007 

0 . 007 

0 . 007 

0.007 

0.007 

0.007 

0 . 007 

Stk NOXc 

ppm 

0-300 

1. 97 

1. 96 

1. 89 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

Stk CDc Gas hscfh 

hscfh 

0-10000 

ppm 

0-1000 

0.55 

0.47 

0.47 

0.47 

0.47 

0.55 

0.47 

0.47 

0.47 

0.47 

0.39 

0.39 

0. 4 7 

0.47 

0.47 

6925.8 

6920.4 

6901.2 

6895 . 2 

6876.0 

6884 . 4 

6862.2 

6867.6 

6868.2 

6877 . 8 

6889. 8 

6888 . 6 

6895. 8 

6887.4 

6901.2 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

MW Lo 

0-1 

79 .. 

80.1 

79 .. 

79. : 

78. : 

79. ! 

79 

78. : 

79 

79 .. 

79. 

79 . . 

79.! 

79 .. 

79 . ! 

2.5 13. 4 1 5.24 17635 0.7 0.73 0.007 1.96 0.51 6912.0 110.0 79.8 

2 . 7 13.43 5.85 17730 0.8 0 . 73 0 . 008 2 . 12 0.63 6965.4 110.0 80. 

2.4 13.39 5.04 17556 0.5 0.72 0 . 007 1.89 0.39 6862.2 110 . 0 78. 

2.1180E+2 1. 1396E+3 4.4566E+2 1. 4 989E+6 5.5600E+1 6.1780E+1 6 .1400E-1 1.6683E+2 4.3630E+1 5.8751E+5 9.3500E+3 6 . 7887E+ 

100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100 . 0 100. 

02/01/2013 16 , 12 2>Summary - I-Min RATA - Continued pag~ 
Data Summary Report 

Company: 

Sourc e : 

Data Group: 

Report Name: 

CPV Sentinel , LLC 

62575 Powerline Road 

Desert Hot Springs, CA 

Turbine 2 

92240 

S~B~\ ~Id" 2- 5-11~\L- tJ\-\;-1-7-2. 

.. v.,p1- TRACE 

Environmental Systems, [nco 

Start of Report : 

2>1-Min Cales 

2>Summary - l-Min RATA 

02/01/2013 11,05 End of Report, 02/01/2013 12,15 validation: All Available Data 

Group#-Channel# 

Long De scrip . 

sho rt Des crip . 

units 

Range 

02/01/2013 11 : 05 

0 2 /01 /2013 11 : 06 

02/01/2013 11:07 

02/01/2013 11:08 

02/01/2013 11:09 

02/01/2013 11:10 

02/01/2013 11:11 

02/01/2013 11:12 

02/01/2013 11:13 

0 2 /01/2013 11:14 

02/01/2013 11:15 

02/01/2013 11:16 

02/01/2013 11:17 

02/01/2013 11:18 

02/01/2013 11:19 

02/01/2013 11:20 

02/01/2013 11:21 

02/01/2013 11:22 

02/01/2013 11:23 

02/01/2013 11:24 

02/01/2013 11:25 

02/01/2013 11:26 

02/01/2013 11:27 

02/01/2013 11;28 

02/01/2013 11:29 

02/01/2013 11:30 

02/01/2013 11:31 

02/01/2013 11;32 

02/01/2013 11:33 

02/01/2013 11:34 

Date/Time Printed: 

G12-C2 G12-C4 G12-C11 

2>Stk NOx 

Stk NOx 

2>Stk 02 2>NOx Mass 

ppm 

0-150 

2.4 

2.5 

2.5 

2.4 

2.4 

2.5 

2.5 

2.4 

2.6 

2.5 

2 . 5 

2 . 3 

2.4 

2.5 

2.5 

2.5 

2 . 5 

2 . 4 

2.6 

2.4 

2.5 

2.5 

2.6 

2.5 

2.5 

2.4 

2.6 

2 . 4 

2.4 

2.4 

Stk 02 

• 

0-25 

13 .4 1 

13 . 40 

13.40 

13 .42 

13 .40 

13 .40 

13 .40 

13 .41 

13.39 

13 .40 

13 . 39 

13.39 

13.41 

13 . 40 

13 .40 

13 .40 

13 . 40 

13 . 41 

13 . 40 

13.40 

13 . 40 

13.39 

13 . 38 

13.40 

13 . 40 

13 .41 

13 .41 

13 .41 

13 . 40 

13 .42 

02/01/2013 16,12 

NOx Mass 

1b/hr 

0-100 

5.13 

5.14 

5.12 

5.10 

5.13 

5.13 

5.13 

5 . 12 

5.85 

5.13 

5.16 

5.15 

5.12 

5 . 11 

5.11 

5.10 

5.11 

5.10 

5.84 

5.11 

5.11 

5 . 11 

5.84 

5.10 

5 . 10 

5 . 09 

5 . 82 

5.08 

5 . 09 

5.08 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

17797 

17827 

17758 

17738 

17778 

17788 

17772 

17774 

17734 

17799 

17870 

17835 

17769 

17716 

17721 

17695 

17715 

17697 

17707 

17704 

17723 

17691 

17677 

17684 

17681 

17657 

17679 

17648 

17646 

17672 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

1.8 

1.6 

1.3 

1.1 

1.6 

1.4 

1.7 

1.5 

1.5 

1.4 

1.6 

1.7 

1.6 

1.5 

1.5 

1.8 

1.6 

1.7 

1.6 

1.7 

1.9 

2.0 

1.2 

1.1 

1.3 

1.3 

1.2 

1.0 

1.0 

1.1 

G12 -C13 G12-C10 G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

2.20 

2.20 

1. 46 

1. 46 

2 . 20 

1. 4 7 

2.20 

2.19 

2.19 

1.47 

2.21 

2.21 

2 . 19 

2.19 

2.19 

2.19 

2.19 

2.18 

2.19 

2.19 

2.19 

2 . 92 

1. 4 6 

1. 46 

1.46 

1. 45 

1. 45 

1. 45 

1.45 

1.45 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0 . 007 

0.00 7 

0.007 

0.007 

0 . 007 

0 . 008 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 89 

1. 97 

1. 97 

1. 89 

1. 89 

1. 97 

1. 97 

1. 89 

2.04 

1. 97 

1.96 

1. 81 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 89 

2.05 

1. 89 

1. 97 

1.96 

2 . 04 

1. 97 

1. 97 

1. 89 

2.05 

1. 89 

1. 89 

1. 89 

G12-C7 G12-C8 

2>Stk CDc 2>Gas Flow 

Stk COc Gas hscfh 

ppm 

0-1000 

1.42 

1. 26 

1. 02 

0.87 

1. 26 

1.10 

1. 34 

1.18 

1.18 

1.10 

1.26 

1.34 

1.26 

1.18 

1.18 

1.42 

1. 26 

1. 34 

1. 26 

1. 34 

1. 49 

1. 57 

0.94 

0.87 

1. 02 

1. 02 

0.95 

0.79 

0.79 

0.87 

hscfh 

0-10000 

6973.8 

6994.8 

6967.8 

6 941.4 

6975.6 

6979.8 

6973.2 

6964 .8 

6967.8 

6984.0 

7021. 2 

7007 . 4 

6963.0 

6951.6 

6953.4 

6943.2 

6951.0 

6934.8 

6948.0 

6946.8 

6954.0 

6 951.0 

6954 .6 

6 939.0 

6 937.8 

6919.2 

6927.6 

6915.6 

6924.0 

6915.6 

G12-C18 

2>NH3 Inj 

NH3Inj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

G12-C 

2>MW Lo 

MW Lo 

0-1 

80 . 1 

80 .. 

80 . 

80.1 

80.1 

80. : 

80. : 

80.1 

80. : 

81.: 

80. 

80.: 

80.1 

79 .. 

80.1 

79 .. 

79. ! 

79. ! 

79. : 

79 .. 

79 . . 

79 .. 

79 . ! 

79 .. 

79 . 

79 . . 

79 .. 

79 . : 

79. : 

79 .. 

pagE 
Group#-Channel# 

Long Descrip . 

Short Descrip. 

Un its 

Range 

02/01/2013 11:35 

02/01/2013 11:36 

02/01/2013 11:37 

02/01/2013 11:38 

02/01/2013 11:39 

02/01/2013 11:40 

02/01/2013 11:41 

02/01/2013 11:42 

02/01/2013 11:43 

02/01/2013 11:44 

02/01/2013 11:45 

02/01/2013 11:46 

02/01/2013 11;47 

02/01/2013 11:48 

02/01/2013 11:49 

02/01/ 2 013 11:50 

02/01/2013 11:51 

02/01/2013 11:52 

02/01/2013 11:53 

02/01/2013 11:54 

02/01/2013 11:55 

02/01/2013 11:56 

02/01/2013 1 1 :57 

02/01/2013 11:58 

02/01/2013 11:59 

02/01/2013 12:00 

02/01/2013 12:01 

02/01/2013 12:02 

02/01/2013 12:03 

02/01/2013 12:04 

02/01/2013 12:05 

02/01/2013 12:06 

02/01/2013 12:07 

02/01/2013 12:08 

02/01/2013 12:09 

02/01/2013 12:10 

02/01/2013 12:11 

02/01/2013 12;12 

02/01/2013 12;13 

02/01/2013 12:14 

Date/Time Printed: 

G12 -C2 G12~C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.4 

2.5 

2.6 

2.5 

2 . 4 

2.6 

2.5 

2.5 

2.5 

2.4 

2.5 

2.5 

2.6 

2.5 

2.6 

2.6 

2.5 

2.5 

2.5 

2.6 

2.6 

2.5 

2.5 

2.5 

2.5 

2.4 

2.4 

2.5 

2.5 

2.5 

2.6 

2.5 

2.3 

2. 4 

2.4 

2.5 

2.3 

2.3 

2.4 

2.4 

Stk 02 

\ 

0-25 

13 .42 

13 .41 

13 .39 

13 .39 

13 .40 

13.39 

13 .40 

13 .40 

13.39 

13.40 

13.41 

13.41 

13.41 

13.40 

13 .4 0 

13.39 

13.39 

13.40 

13.40 

13. 40 

13 .40 

13 .40 

13 .39 

13 .40 

13.39 

13.39 

13.40 

13.38 

13.38 

13 .39 

13.38 

13 .38 

13 .40 

13.39 

13.39 

13.37 

13.39 

13.40 

1 3.39 

13 .38 

02/01/2013 16012 

NOx Mass 

Ib/hr 

0-100 

5.09 

5.09 

5.83 

5.10 

5.09 

5.84 

5.08 

5.08 

5.10 

5.07 

5.08 

5.09 

5.80 

5.07 

5.80 

5.80 

5.08 

5.06 

5.07 

5.79 

5.80 

5.07 

5.09 

5.07 

5.07 

5.08 

5.07 

5.09 

5.08 

5.09 

5.82 

5.11 

5.11 

5.11 

5.10 

5.12 

5.11 

5.10 

5.10 

5.09 

StkFlow 

kscfh 

0-300000 

17695 

17665 

17672 

17659 

17645 

17697 

17626 

17629 

17646 

17586 

17622 

17656 

17633 

17571 

17593 

17566 

17577 

17559 

17576 

17580 

17591 

17585 

17642 

17 596 

17571 

17586 

17568 

17589 

17566 

17629 

17618 

17683 

17703 

17708 

17655 

17689 

17696 

17694 

17646 

17616 

G12-C) G12-C13 G12 -CI0 G12-C6 G12-C7 G12 - C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

1.3 

1.1 

1.3 

1 4 

1.1 

1.0 

0 .8 

0. 9 

0.8 

0.8 

0.7 

0.6 

0.6 

0.6 

0.6 

0.6 

0.6 

0.5 

0.4 

0.4 

0.4 

0.3 

0.3 

0.2 

0 . 1 

0.2 

0.2 

0.2 

0.2 

0.1 

0.2 

0.1 

0.2 

0.2 

0.2 

0.1 

0 .2 

0. 2 

0.2 

0.2 

CO Mass 

Ib/hr 

0-100 

1.45 

1.45 

l.46 

l. 46 

l. 45 

1.46 

0.73 

1. 45 

0 .73 

0.72 

0.73 

0 . 73 

0.73 

0.72 

0.72 

0.72 

0.73 

0.72 

0.72 

0.72 

0.72 

0. 72 

0.73 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0 . 00 

0.00 

0.00 

0.00 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.008 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.008 

0.008 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

l. 89 

1. 97 

2.04 

l. 96 

l. 89 

2.04 

l. 97 

1. 97 

1. 96 

1. 89 

l. 97 

1. 97 

2.05 

1. 97 

2.05 

2.04 

1. 96 

l. 97 

1. 97 

2.05 

2.05 

1. 97 

1.96 

l. 97 

1. 96 

1. 89 

1. 89 

l. 96 

l. 96 

l. 96 

2.04 

1. 96 

l. 81 

l. 89 

1. 89 

1. 96 

l. 81 

l. B1 

1. B9 

l. BB 

Stk COe Gas 

ppm 

hscfh 

hscfh 

0-1000 

l. 03 

0.87 

l. 02 

l.10 

0.87 

0.79 

0.63 

0.71 

0.63 

0.63 

0 . 55 

o 47 

0 .4 7 

0.47 

0.47 

0.47 

0.47 

0.39 

0.31 

0.31 

0.31 

0.24 

0.24 

0.16 

0.08 

0.16 

0.16 

0 . 16 

0.16 

0.08 

0.16 

0.08 

0.16 

0.16 

0.16 

0.08 

0.16 

0.16 

0.16 

0 . 16 

0-10000 

6924.6 

6922.2 

6943.2 

6938.4 

6923.4 

6953.4 

6916.2 

6917.4 

6933.0 

6900.6 

6905.4 

6918.6 

6909.6 

6894.6 

6903.0 

6901.8 

6906.0 

6889.8 

6896.4 

6B98.2 

6902.4 

6900.0 

6931. 8 

6904 .2 

6903.6 

6909.6 

6893.4 

6919.8 

6910.8 

6926.4 

6931.2 

6957.0 

6946.2 

6957.6 

6936.6 

6968.4 

6952.8 

6942.6 

6933.0 

6930.6 

NH3Inj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

llO.O 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

l10.0 

llO.O 

110.0 

l10.0 

110.0 

110.0 

2>Summary - 1-Min RATA - Continued 

MW La 

0 - 1 

79.: 

79 . . 

80.1 

79. : 

79. ' 

80.1 

79 .. 

79 

79. ! 

79.: 

79. : 

79.! 

79 .. 

79 .. 

79 .. 

79. : 

79.: 

79. ! 

79. : 

79 . : 

79. : 

79 . . 

79 .. 

80 . 1 

79. : 

79 .. 

79. 

80.1 

79 . 

79 . . 

80. ( 

80 . . 

80. ( 

80. 

79. : 

80 .. 

80 . ! 

80. : 

79. : 

80. : 

pagE 
Group#-Channel# G12 - C2 G12-C4 G12 -C11 G12-C20 G12-C3 G12 -C13 G12 - C10 G12-C6 G1 2-C7 G12 - C8 G12 - C18 G12 - C 

Long Descrip. 2>Stk NOx 2;:.Stk 02 2;:.NOx Mass 2;:.StkFlow 2;:.Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2;:.Gas Flow 2;:.NH3 Inj 2>MW Lo 

Short Descrip . Stk NOx Stk 02 NOx Mass StkFlow Stk CO CO Mass NOx Rate Stk NOXe Stk COe Gas hsefh NH3Inj MW Lo 

Units ppm • Ib/hr ksefh ppm Ib/hr Ib/mmBtu ppm ppm hsefh Ib/hr 

Range 0-150 0-25 0-100 0-300000 0 -1 000 0-100 0-1 0-300 0-1000 0-10000 0-1000 0-1 

02/01/2013 12:15 2.4 13.38 5.09 17619 0.2 0.00 0.007 1. 88 0.16 6931.8 110.0 80. : 

Period Average 2.S 13.40 5.22 17671 0 . 9 1.12 0.007 1. 95 0.72 6936.2 110.0 79.8 

Period Max Value 2.6 13.42 5.85 17870 2.0 2.92 0.008 2.05 1. 57 7021.2 110.0 8l. 

Period Min Value 2.3 13.3 7 5.06 17559 0.1 0.00 0.007 1. 81 0 . 08 6889.8 110.0 79. 

Period Totals = 1.7580E+2 9.5122E+2 3 . 7069E+2 1.2546E+6 6.4600E+1 7 . 9480E+1 5.0900E-1 1.3831E+2 5.0890E+1 4.9246E+5 7.8100E+3 5.6660E+ 

Period % Recovery 100.0 100 . 0 100.0 100.0 100.0 100.0 100.0 100.0 100 . 0 100.0 100.0 100. 

Date/Time Printed: 02/01/2013 16,12 2>Summary - I - Min RATA - Continued pag~ 
Data Summary Report 

Company: CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 

Source: 

Data Group: 

Report Name : 

Turbine 2 

2>1-Min Cales 

92240 

~+1l\Ll G .. if 1-

[2km (2....t\ I CoWl{'fiWiL(.. /0(1/0 TRACE 

Environmental Systems, Inc. 

Start of Report: 

2> I-Min Summary - RATA 

01/30/2013 11,01 End of Report, 01/30/2013 12,17 Validation: All Available Data 

Group#-Channel# 

Long Descrip. 

Short Descrip. 

Units 

Range 

01/30/2013 11:01 

01/30/2013 11:02 

01/30/2013 11:03 

01/30/2013 11:04 

01/30/2013 11:05 

01/30/2013 11:06 

01/30/2013 11:07 

01/30/2013 11;08 

01/30/2013 11;09 

01/30/2013 11;10 

01/30/2013 11:11 

01/30/2013 11:12 

01/30/2013 11:13 

01/30/2013 11:14 

01/30/2013 11:15 

01/30/2013 11:16 

01/30/2013 11:17 

01/30/2013 11:18 

01/30/2013 11:19 

01/30/2013 11:20 

01/30/2013 11:21 

01/30/2013 11:22 

01/30/2013 11:23 

01/30/2013 11:24 

01/30/2013 11:25 

01/30/2013 11:26 

01/30/2013 11:27 

01/30/2013 11:28 

01/30/2013 11:29 

01/30/2013 11:30 

Date/Time Printed: 

G12-C2 G12-C4 Gl2-ell 

2>Stk NOx 

Stk NOx 

2 >Stk 02 2 >NOx Mass 

ppm 

0-150 

3.0 

2.9 

3.0 

3.0 

3.0 

3.0 

3.0 

3.0 

2.8 

3.0 

2.9 

2.8 

2.8 

3.0 

2.8 

3.0 

2.8 

3.1 

2.8 

2.9 

2.8 

2.9 

2.9 

2.9 

2.8 

2.9 

3.0 

2.9 

2.9 

2.9 

Stk 02 

• 

0-25 

13.02 

13.02 

13.02 

13.03 

13.01 

13.02 

13.03 

13.03 

13.04 

13.03 

13.04 

13.05 

13.05 

13.04 

13.05 

13.04 

13.05 

13.02 

13.04 

13.05 

13.06 

13.06 

13.05 

13.04 

13.03 

13.03 

13.02 

13.03 

13.02 

13.03 

01/30/2013 13 ,14 

NDx Mass 

Ib/hr 

0-100 

7.11 

7.10 

7.10 

7.11 

7.12 

7.10 

7.10 

7.09 

7.09 

7.10 

7.08 

7.07 

7.06 

7.06 

7.05 

7.06 

7.07 

7.96 

7.05 

7.08 

7.07 

7.08 

7.08 

7.08 

7.09 

7.09 

7.10 

7.08 

7.08 

7.06 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20528 

20492 

20506 

20544 

20546 

20511 

20525 

20505 

20532 

20540 

20496 

20493 

20478 

20427 

20434 

20430 

20483 

20425 

20419 

20515 

20512 

20541 

20516 

20494 

20486 

20499 

20487 

20476 

20435 

20409 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

3.2 

3.3 

3.2 

3.3 

3.2 

3.2 

3.2 

3.0 

3.1 

3.1 

3.2 

3.3 

3.6 

3.4 

3.1 

3.2 

2.9 

3.4 

2.4 

3.S 

3.7 

3.7 

3.S 

3.0 

3.0 

2.9 

2.9 

2.8 

2.8 

3.0 

G12 - CD GIZ-ClD G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NDXc 

co Mass 

1b/hr 

0-100 

4.44 

5.32 

4.44 

5.33 

4.45 

4.44 

4.44 

4.43 

4.43 

4.44 

4.43 

5.30 

5.30 

5.29 

4.41 

4.41 

4.42 

5.30 

3.53 

5.31 

5.30 

5.31 

5.31 

4.42 

4.43 

4.43 

4.43 

4.43 

4.42 

4.41 

NDx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.009 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

Stk NOXc 

ppm 

0-300 

2.25 

2.17 

2.25 

2.25 

2.24 

2.25 

2.25 

2.25 

2.10 

2.25 

2.18 

2.10 

2.10 

2.25 

2.10 

2.25 

2.10 

2.32 

2.10 

2.18 

2.11 

2.18 

2.18 

2.18 

2.10 

2.17 

2.25 

2.17 

2.17 

2.17 

G12-C7 G12 - CB 

2>Stk CDc 2>Gas Flow 

Stk CDc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

2.40 

2.47 

2.40 

2.47 

2.39 

2.40 

2.40 

2.25 

2.33 

2.32 

2.40 

2.48 

2.71 

2.55 

2.33 

2.40 

2.18 

2.55 

1. 80 

2.63 

2.78 

2.78 

2.63 

2.25 

2.25 

2.17 

2.17 

2.10 

2.10 

2.25 

8463.0 

8448.0 

8454.0 

8458.8 

8481.0 

8455.8 

8451.0 

8442.6 

8443.2 

8457.0 

8428.2 

8416.2 

8410.2 

8400.0 

8392.2 

8401.2 

8412.0 

8420.4 

8396.4 

8425.2 

8413.2 

8425.2 

8425.8 

8427.6 

8434.8 

8440.2 

8446.2 

8430.6 

8424.6 

8403.0 

GI2 - C1S 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

G12-C 

2>MW La 

MW La 

0-1 

102. ' 

10 2.: 

103.: 

102. ' 

103.: 

102. : 

103.1 

102. ' 

103.1 

102. : 

102.: 

102. 

102 

102 .. 

101.: 

102 . ! 

102.: 

102. : 

102.1 

102. : 

102.1 

102.1 

102. ' 

102. : 

102. : 

102. : 

102 .. 

102 . : 

102.: 

102.1 

PagE 
Group#-Channel# 

Long Descrip. 

Short vescrip. 

Units 

Range 

01/30/2013 11;31 

01/30/2013 11;32 

01/30/2013 11:33 

01/30/2013 11:34 

01/30/2013 11;35 

01/30/2013 11:36 

01/30/2013 11:37 

01/30/2013 11:38 

01/30/2013 11:39 

01/30/2013 11:40 

01/30/2013 11:41 

01/30/2013 11:42 

01/30/2013 11:43 

01/30/2013 11:44 

01/30/2013 11:45 

01/30/2013 11:46 

01/30/2013 11:47 

01/30/2013 11:48 

01/30/2013 11:49 

01/30/2013 11:50 

01/30/2013 11:51 

01/30/2013 11:52 

01/30/2013 11:53 

01/30/2013 11:54 

01/30/2013 11:55 

01/30/2013 11:56 

01/30/2013 11:57 

01/30/2013 11:58 

01/30/2013 11:59 

01/30/2013 12:00 

01/30/2013 12:01 

01/30/2013 12;02 

01/30/2013 12:03 

01/30/2013 12;04 

01/30/2013 12:05 

01/30/2013 12:06 

01/30/2013 12:07 

01/30/2013 12:08 

01/30/2013 12;09 

01/30/2013 12:10 

Date/Time Printed: 

G12-C2 G12 - C4 G12 - Cl1 G1 2 - C20 

2>Stk NOx 

Stk NOx 

2>Stk 02 2>NOx Mass 2>StkFlow 

ppm 

0-150 

3.0 

2.9 

2.9 

2.8 

3.0 

3.0 

2.9 

3.0 

3.0 

3.1 

3.0 

2.9 

2.9 

2.9 

2.9 

3.0 

3.0 

2.9 

2.9 

2.9 

2.9 

2.9 

2.9 

3.0 

3.0 

3.0 

3.0 

2.9 

3.0 

2.9 

3.0 

3.0 

2.9 

2.9 

2.9 

2.9 

3.0 

2.9 

2.9 

3.0 

stk 02 

• 

0-25 

13.03 

13.03 

13.02 

13.02 

13.02 

13.02 

13.02 

13.01 

13.02 

13.00 

13.00 

13.01 

13.01 

13. 01 

13.02 

13.01 

13.02 

13. 02 

13.02 

13.02 

13.02 

13.02 

13.01 

13.00 

13.00 

13.00 

13.01 

13.02 

13.00 

13.01 

13.00 

12.99 

13. 01 

13.00 

13.00 

12.99 

13.00 

12.99 

12.99 

12.98 

01/30/2013 13,14 

NOx Mass 

I b/hr 

0-100 

7.08 

7.07 

7.09 

7.09 

7.09 

7.09 

7.09 

7 . 08 

7.08 

7.99 

7.10 

7 . 08 

7.09 

7.08 

7.08 

7.07 

7.08 

7.08 

7.06 

7.07 

7.07 

7.06 

7.06 

7.08 

7.09 

7.0B 

7.09 

7.07 

7.10 

7.09 

7.10 

7.11 

7.10 

7 . 09 

7.09 

7.09 

7.09 

7.11 

7.10 

7.12 

StkFlow 

kscfh 

0-300000 

20463 

20448 

20479 

20476 

20485 

20476 

20469 

20432 

20457 

20465 

20439 

20415 

20437 

20421 

20451 

20389 

20441 

20434 

20393 

20407 

20428 

20384 

20371 

20380 

20409 

20401 

20448 

20422 

20456 

20459 

20441 

20462 

20469 

20430 

20431 

20407 

20421 

20440 

20430 

20442 

G12-C3 G12 - C13 G12-C10 G12 - C6 G12 - C7 G12 - C8 G12 - C18 G12 - C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

2.9 

2.8 

2.8 

2.8 

2.7 

2.8 

2.8 

2.8 

2.8 

2.7 

2.8 

2.8 

2.7 

2.7 

2.9 

2.8 

2.7 

2.7 

2.8 

2 . 7 

2.8 

2.8 

2.8 

2.7 

2.7 

2.7 

2.7 

2.8 

2.6 

2.8 

2.6 

2.6 

2.7 

2.6 

2.7 

2.6 

2.7 

2.5 

2.7 

2.4 

CO Mass 

Ib/hr 

0 - 100 

4.42 

4.42 

4.43 

4.43 

4.43 

4.43 

4.43 

4.43 

4.43 

4.44 

4.44 

4.42 

4.43 

4.43 

4.43 

4.42 

4.42 

4.42 

4.41 

4.42 

4.42 

4.41 

4.41 

4.42 

4.43 

4.43 

4.43 

4.42 

3.55 

4.43 

3.55 

3.56 

4.44 

3.55 

4.43 

3.55 

4.43 

3.55 

4.44 

3.56 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.009 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0.008 

0.008 

Stk NOXe 

ppm 

0 - 300 

2.25 

2.17 

2.17 

2.10 

2.25 

2.25 

2.17 

2.24 

2.25 

2.32 

2.24 

2.17 

2.17 

2.17 

2.17 

2.24 

2.25 

2.17 

2.17 

2.17 

2.17 

2.17 

2.17 

2.24 

2.24 

2.24 

2.24 

2.17 

2.24 

2.17 

2.24 

2.24 

2.17 

2.17 

2.17 

2.16 

2.24 

2.16 

2.16 

2.23 

Stk COe Gas hsefh 

ppm hscfh 

0-1000 0-10000 

2.17 8425.2 

2.10 8419.2 

2.10 8442.6 

2.10 8441.4 

2.02 8445.0 

2.10 8441.4 

2.10 8438 . 4 

2.09 8434.2 

2.10 8433.6 

2.02 8458.2 

2.09 8447.4 

2.09 8427 . 0 

2.02 8436.0 

2.02 8429.4 

2.17 8431.2 

2.09 8416.2 

2.02 8427.0 

2.02 8424.0 

2.10 8407.2 

2.02 8413.2 

2.10 8421.6 

2.10 8403.6 

2.09 8409.0 

2.02 8423.4 

2.02 8435.4 

2.02 

2.02 

2.10 

1. 94 

2.09 

1. 94 

1. 94 

2.02 

1. 94 

2.02 

1. 94 

2.02 

1. 86 

2.01 

1. 79 

8431.8 

8440.8 

8419.2 

8454.6 

8445.0 

8448.6 

8467.8 

8449.2 

8443.8 

8444.4 

8445.0 

8440.2 

8458 . 8 

8454.6 

8470.2 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2> I-Min Summary - RATA - Continued 

MW Lo 

0 - 1 

1 02.! 

102 . : 

102 .. 

102. ! 

102 . . 

102. : 

102 .. 

102. : 

102 .: 

102. l 

103. 1 

102.! 

102. : 

102.l 

103.: 

102.: 

102 .: 

102 . . 

102. 

102. : 

102 .. 

102.: 

102. ! 

102. : 

102.l 

102. 

102. 

102 . : 

103. : 

102 . . 

102 

103. : 

102.: 

102. : 

102. ! 

102. : 

102.: 

103. t 

103 .. 

103 . . 

Pagt 
Group#-Channel# 

Long Descrip. 

Short Des cri p. 

Units 

Range 

01/30/2013 12:11 

01/30/2013 12:12 

01/30/2013 12:13 

01/30/2013 12:14 

01/30/2013 12:15 

01/30/2013 12:16 

01/30/2013 12:17 

Peri od Average 

Peri od Max Value 

Period Min Value 

Period Totals "" 

Pe riod % Recovery 

Date/Time Printed: 

G12-C2 G12-C4 G12-C11 G12 - C20 G12-C3 GI2 - Cl3 GI2 - CIO G12 - C6 G12-C7 GI2-CB GI2-CIS G1 2 - C 

2:>Stk NOx 

Stk NOx 

2:>Stk 02 2 :>NOx Mass 2:>StkFlow 2:>Stk CO 2:>CO Mass 2:>NOx Rate 2:>Stk NOXe 2:>Stk COe 2:>Gas Flow 2:>NH3 Inj 2:>MW Lo 

ppm 

0-150 

2.9 

3.0 

3.0 

2.9 

Stk 02 

• 

0-25 

13.00 

12.98 

12.97 

12.98 

NOx Mass 

Ib/hr 

0-100 

7.10 

7.13 

7.14 

7.12 

StkFlow 

kscfh 

0-300000 

20460 

20477 

20494 

20456 

Stk CO 

ppm 

0 - 1000 

2 . 6 

2.5 

2.5 

2.6 

CO Mass 

Ib/hr 

0-100 

3.55 

3.56 

3.57 

3.56 

NOx Rate 

Ib/mmBtu 

0-1 

O.OOB 

0.008 

0.008 

0.008 

Stk NOXe 

ppm 

0 - 300 

2.17 

2.23 

2.23 

2.16 

3.1 12.98 8.00 20429 2.4 3.56 0.009 2.31 

3.1 12.97 7.14 20490 2.6 3.57 0.008 2.31 

3.1 12.97 7.13 20447 2.3 3.56 0.008 2.31 

2.9 13.02 7.12 20459 2.9 4.37 0 . 008 2.20 

3.1 13.06 8.00 20546 3.7 5.33 0.009 2.32 

2.8 12.97 7.05 20371 2 . 3 3 . 53 0.008 2.10 

2.2640E+2 1. 0022E+3 5.4846E+2 1. 5753E+6 2.2160E+2 3. 3662E+2 6.1900E-1 1. 6942E+2 

100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 

Stk COe Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1. 94 

1. 86 

1. 86 

1. 94 

1. 79 

1. 93 

1. 71 

2.15 

2.78 

1. 71 

1.6589E+2 

100.0 

8456.4 

8484.6 

8502.6 

8476.2 

8464.8 

8500.8 

8482.8 

8438.2 

B502.6 

8392.2 

6.4974E+5 

100.0 

NH3Inj 

Ib/hr 

0 - 1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

8.4700E+3 

100.0 

01/30/2013 13,14 2:> l-Min Summary - RATA - Continued 

MW Lo 

0 - 1 

102. : 

103. : 

104.1 

103 . . 

103. : 

103. ! 

103. : 

102.6 

104. 

101. 

7.9037E+ 

100. 

Pagt 
Data Summary Report 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 

Source : Turbine 2 

Data Group : 2>1-Min Cales 

Report Name : 2>Summary - I-Min RATA 

St art of Report : 01/30/2013 13,11 

G12-C4 

92240 

7CU1 foll.\ ~ t L 

(lfM- ~ ... '2 

~' \~ ~Q1~4n't End of Report, 01/30/2013 15 , 05 

GI2 - CII G12-C20 G12-C3 G12-C13 GI2-CIO 

TRACE 

/CO I/o 

Ellvironmelltal Systems, ItIC. 

Validation: Valid Data Only 

Group#-Channel# G12-C6 G12-C7 G12 - Ca GI2 -ClS G12-C 

Long Descrip . 

Short Descrip . 

Units 

G12-C2 

2>stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 2>Stk co 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk CDc 2>Gas Flow 2>NH3 Inj 2>MW La 

Range 

01/30/2013 13:11 

01/30/2013 13:12 

01/30/2013 13:13 

01/30/2013 13:14 

01/30/2013 13:15 

01/30/2013 13:16 

01/30/2013 13:17 

01/30/2013 13:18 

01/30/2013 13:19 

01/30/2013 13:20 

01/30/2013 13:21 

01/30/2013 13:22 

01/30/2 013 1 3:23 

01/30/ 2013 13:24 

01/30/2013 13:25 

01/30/2013 13:26 

01/30/2013 13:27 

01/30/2013 13;28 

01/30/2013 13:29 

01/30/2013 13:30 

01/30/2013 13:31 

01/30/ 2013 13:32 

01/30/2013 13:33 

01/30/2013 13:34 

01/30/2013 13:35 

01/30/2013 13:36 

01/30/2013 13:37 

01/30/2013 13:38 

01/30/2013 13:39 

01/30/2013 13:40 

Date/Time Printed: 

2.8 

2.8 

2.9 

2.8 

2.8 

2.7 

2.8 

2.8 

2.8 

2.8 

2.8 

2.8 

2.7 

2.8 

2.7 

2.8 

2.7 

2.9 

2.9 

2.8 

2.9 

2.9 

2.9 

2.9 

2.8 

2.8 

2.8 

2.7 

2.7 

2.8 

Stk 02 

• 

0- 2 5 

12.96 

12.95 

12.94 

12.96 

12 . 95 

12 .96 

12.95 

12.94 

12 . 94 

12.95 

12.96 

12.96 

12.96 

12. 96 

12.96 

12.96 

12.97 

12.94 

12.91 

12.93 

12.93 

12.93 

12 . 92 

12.92 

12.93 

12.93 

12.94 

12.96 

12.95 

12.95 

01/31/2013 12,20 

NOx Mass 

Ib/hr 

0 -100 

7.10 

7.12 

7.13 

7.11 

7.11 

6.22 

7.10 

7.11 

7.09 

7.10 

7 . 09 

7.08 

6.20 

7.08 

6.20 

7.08 

6.19 

7.12 

7.16 

7.15 

7.14 

7.15 

7.14 

7.14 

7.15 

7.13 

7.12 

6.21 

6.21 

7.10 

StkFlow 

kscfh 

0-300000 

20356 

20375 

20384 

20366 

20359 

20360 

20309 

20325 

20274 

20327 

20310 

20304 

20302 

20 2 88 

20317 

20285 

20308 

20368 

20395 

20400 

20391 

20 4 1 4 

20370 

20363 

20403 

20361 

20355 

20337 

20320 

20333 

Stk co 

ppm 

0-1000 

2 .5 

2.6 

2.5 

2.6 

2.6 

2.8 

2.6 

2.9 

2.7 

2.7 

2.7 

2.8 

2.8 

2.7 

3.0 

2.7 

2.9 

2.9 

2.6 

2.8 

2.6 

2.6 

2.8 

2.5 

2.5 

2.8 

2.6 

2 .5 

2.9 

2.7 

CO Mass 

Ib/hr 

0 - 100 

3.55 

).56 

3.57 

3.55 

3.56 

4.44 

3.55 

4.44 

3.55 

3.55 

3.54 

4.43 

4.43 

3.54 

4.43 

3.54 

4.42 

4.4 5 

3.58 

4.47 

3.57 

3.58 

4.47 

3.57 

3.57 

4.46 

3.56 

3.55 

4.44 

3.55 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.007 

0.008 

Stk NOXc 

ppm 

0 - 300 

2.08 

2.08 

2.15 

2.08 

2.08 

2.01 

2.08 

2.08 

2.08 

2.08 

2.08 

2.08 

2.01 

2.08 

2. 01 

2.08 

2.01 

2.15 

2.14 

2.07 

2.15 

2.15 

2.14 

2.14 

2.07 

2.07 

2.08 

2.01 

2.00 

2.08 

Stk COe Gas hsefh 

ppm hsefh 

0-1000 0-10000 

1.86 8455.8 

1.93 8474.4 

1.85 8488.8 

1.93 8460.0 

1.93 8467.8 

2 . 08 8457.6 

1.93 8446.8 

2.15 8464.2 

2.00 8443.2 

2.00 8454.6 

2.01 8436.6 

2.08 8434.2 

2. 08 8433.6 

2 .01 8427.6 

2.23 8439.6 

2.01 8426.4 

2.16 8425.2 

2.15 8482.2 

1.92 8525.4 

2.07 8506.2 

1.92 8502.6 

1. 92 

2 . 07 

1. 85 

1. 85 

2.07 

1. 93 

1. 86 

2.15 

2.00 

8512.2 

8504. 4 

8501.4 

8507.4 

8490.0 

8476.8 

8448.0 

8451.6 

8457.0 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

63.2 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110. 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

MW Lo 

0-1 

103.: 

103. : 

103. 

103. ( 

103 .. 

102.1 

102.: 

103.: 

102 .. 

102 .. 

103.! 

102 .. 

102 . . 

10 2 .. 

102 .. 

102. ! 

102.' 

103.~ 

104.' 

103. 

103. ' 

103.' 

103,! 

103.' 

103. 

1 03,! 

103 

102,' 

103.: 

102.' 

Pagt 
Group#-Channel# 

Long Descrip . 

Short Desc r i p. 

Units 

Range 

01/30/2013 13:41 

01/30/2013 13:42 

01/30/2013 13:43 

01/30/2013 13:44 

01/30/2013 13:45 

01/30/2013 13:46 

01/30/2013 13:47 

01/30/2013 13:48 

01/30/2013 13:49 

01/30/2013 13:50 

01/30/2013 13:51 

01/30/2013 13:52 

01/30/2013 13:53 

01/30/2013 13:54 

01/30/2013 13:55 

01/30/2013 13:56 

01/30/2013 13:57 

01/30/2013 13;58 

01/30/2013 13:59 

01/30/2013 14:00 

01/30/2013 14:01 

01/30/2013 14:02 

01/30/2013 14:03 

01/30/2013 14:04 

01/30/2013 14;05 

01/30/2013 14:06 

01/30/2013 14:07 

01/30/2013 14:0B 

01/30/2013 14:09 

01/30/2013 14:10 

01/30/2013 14:11 

01/30/2013 14:12 

01/30/2013 14:13 

01/30/2013 14:14 

01/30/2013 14:15 

01/30/2013 14:16 

01/30/2013 14:17 

01/30/2013 14:1B 

01/30/2013 14:19 

01/30/2013 14:20 

Date/Time Printed: 

G12 - C2 G12-C4 

2>Stk NOx 2>Stk 02 

Stk NOx Stk 02 

ppm • 

0-150 0-25 

2.8 12.95 

2.7 12.96 

2.7 12.95 

2.7 12.95 

2.8 12.95 

01/31/2013 12,20 

G12-C11 

2>NOx Mass 

NOx Mass 

Ib/hr 

0-100 

7.09 

6.20 

6.20 

6.20 

7.10 

G12-C20 G12-C3 G12-Cl3 

2>StkFlow 2>Stk CO 2>CO Mass 

StkFlow Stk CO cb Mass 

kscfh ppm Ib/hr 

0-300000 0 -1000 0-100 

20306 2.7 3.55 

20301 2.7 3.54 

20293 2 . ' 4.43 

20270 2.8 4.43 

20332 3.0 4.44 

G12-CI0 G12-C6 G12-C7 G12 - C8 G12-C18 G12-C 

2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW La 

NOx Rate Stk NOXe Stk COe Gas hsefh NH3Inj MW La 

Ib/mmBtu ppm ppm hscfh Ib/hr 

0-1 0 -3 00 0-1000 0-10000 0-1000 0-1 

0.008 2.08 2.00 8445.6 110.0 103 .. 

0.007 2.01 2.01 8433.0 110.0 103.4 

0.007 2.00 2.15 B440.2 110.0 102. 

0.007 2.00 2.08 8430.6 110.0 103.4 

O.OOB 2.0B 2.23 B456.4 110.0 102. ' 

2>Summary - l-Min RATA - Continued PagE 
Group# - Channel# 

Long Descrip . 

Short Descri p . 

Units 

Range 

01/30/2013 14:21 

01/30/2013 14:22 

01/30/2013 14:23 

01/30/2013 14:28 

01/30/2013 14 :29 

01/30/2013 14 :30 

01/30/2013 14:31 

01/30/2013 14:32 

01/30/2013 14:33 

01/30/2013 14:34 

01/30/2013 14:35 

01/30/2013 14:36 

01/30/2013 14:37 

01/30/2013 14:38 

01/30/2013 14:39 

01/30/2013 14:40 

01/30/2013 14:41 

01/30/2013 14:42 

01/30/2013 14:43 

01/30/2013 14:44 

01/30/2013 14:45 

01/30/2013 14:46 

01/30/2013 14:47 

01/30/2013 14:48 

01/30/2013 14:49 

01/30/2013 14:50 

01/30/2013 14:51 

01/30/2013 14:52 

01/30/2013 14:53 

01/30/2013 14:54 

01/30/2013 14:55 

01/30/2013 14:56 

01/30/2013 14:57 

01/30/2013 14:58 

01/30/2013 14:59 

01/30/2013 15:00 

01/30/2013 15:01 

01/30/2013 15:02 

01/30/2013 15:03 

01/30/2013 15:04 

Date/Time Printed: 

G12 -C2 G12-C4 G12-Cl1 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.5 

2.6 

2.5 

2.6 

2.6 

2.6 

2.7 

2.5 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.6 

2.7 

Stk 02 

• 

0-25 

12.95 

12.95 

12.95 

12.95 

12.94 

12.96 

12.95 

12.97 

12.96 

12.96 

12.96 

12.97 

12.96 

12.96 

12.95 

12.95 

12.96 

12.95 

12.94 

12.94 

12.95 

12.95 

12.94 

12.95 

12.95 

12.95 

12.95 

12 . 96 

12.94 

12.95 

12.95 

12.96 

12.96 

12.95 

12 . 95 

12.95 

12.95 

01/31/2013 12,20 

NOx Mass 

Ib/hr 

0-100 

6.20 

6.19 

6.19 

6.19 

6.18 

6.18 

6.16 

6.17 

6.17 

6.17 

6.17 

6.17 

6.17 

6.18 

6.18 

6.18 

6.18 

6.18 

6.19 

6.19 

6.18 

6 .18 

6.19 

6.17 

6.19 

6.19 

6.18 

6.18 

6 . 18 

6.18 

6.18 

6.16 

6.17 

6.17 

6.17 

6.17 

6.18 

StkFlow 

ksefh 

0-300000 

20288 

20238 

20261 

20234 

20205 

20232 

20167 

20225 

20210 

20206 

20207 

20224 

20197 

20249 

20228 

20231 

20237 

20231 

20210 

20212 

20218 

20215 

20218 

2 0197 

20261 

20254 

20215 

20243 

20201 

20222 

20203 

20167 

20197 

20180 

20186 

20189 

20225 

G12-C3 G12 - Cl3 G12-C10 G12-C6 G12-C7 G12 - C8 G12-C18 G12-C . 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

2.0 

1.9 

1.9 

2.0 

1.9 

1.9 

1.8 

1.8 

1.6 

1.6 

1.7 

1.7 

1.5 

1.6 

1.5 

1.6 

1.4 

1.5 

1.5 

1.5 

1.6 

1.7 

1.7 

1.5 

1.7 

1.5 

1.4 

1.6 

1.5 

1.6 

1.6 

1.5 

1.5 

1.6 

1.4 

1.5 

1.4 

CO Mass 

1b/hr 

0-100 

2.66 

2.65 

2.65 

2.65 

2.65 

2.65 

2.64 

2.64 

2.64 

2.64 

2.64 

2.64 

1. 76 

2.65 

1. 77 

2.65 

1. 77 

1. 77 

1. 77 

1. 77 

2.65 

2.65 

2.65 

1. 76 

2.65 

1. 77 

1. 77 

2.65 

1. 77 

2.65 

2.65 

1. 76 

1. 76 

2.64 

1. 76 

1. 76 

1. 77 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1. 86 

1. 93 

1. 86 

1. 93 

1. 93 

1. 93 

2.00 

1. 86 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

1. 93 

2.00 

2.00 

1. 93 

2.00 

2.00 

2.00 

1. 93 

2.00 

2.00 

2.00 

1. 93 

2.01 

1. 93 

2.00 

1. 93 

2.00 

Stk COe Gas hsefh 

ppm hscfh 

0-1000 0-10000 

1. 48 

1.41 

1.41 

1.48 

1.41 

1.41 

1. 34 

1. 34 

1.19 

1.19 

1.26 

1. 26 

1.11 

1.19 

1.11 

1.19 

1. 04 

1.11 

1.11 

1.11 

1.19 

1.26 

1.26 

1.11 

1.26 

1.11 

1. 04 

1.19 

1.11 

1.19 

1.19 

1.11 

1.11 

1.19 

1. 04 

1.11 

1. 04 

8438.4 

8417.4 

8427.0 

8415.6 

8414.4 

8404.2 

8388.0 

8391.0 

8395.2 

8393.4 

8394.0 

8390.4 

8389 . 8 

8411.4 

8413.2 

8414.4 

8406 .6 

8414.4 

8416.2 

8417.4 

8409.0 

8407.8 

8419.8 

8400.6 

8427.0 

8424.0 

8407.8 

8409.0 

8412.6 

8410.8 

8403.0 

8377.2 

8389.8 

8393.4 

8395.8 

8397.0 

8412.0 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110. 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

MW Lo 

0-1 

103 .. 

1 02. ! 

102. ' 

102 . . 

102 

102 . . 

101. 

102.: 

1 02.1 

1 02. : 

101.: 

101 .. 

102.1 

102 . . 

102. : 

102 . . 

102. ' 

102. ! 

102. : 

102 . . 

102 . . 

102. 

102.1 

102.1 

102. ! 

102 .. 

102. ! 

102. 

102 .. 

102. 

102. 

102 .. 

102. : 

102 .. 

102. f 

102.1 

102. 

Pag( 
Group#-Channel# G12-C2 G12-C4 G12-Cl1 G12-C20 G12-C3 G12-C13 G12-ClO Gl2-C6 G12 -C7 G12 -CB G12-CIB GI2-C 

Long Descrip. 2>Stk NOx 2>St:k 02 2>NOx Mass 2>StkFlow 2>St:k CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Short Descrip . Stk NOx Stk 02 NOx Mass StkFlow Stk CO CO Mass NOx Rate Stk NOXc Stk CDc Gas hscfh NH3Inj MW Lo 

Units ppm • 1b/hr kscfh ppm lb/hr lb/mmBtu ppm ppm hscfh 1b/hr 

Range 0 -1 50 0-25 0-100 0-300000 0-1000 0-100 0-1 0-300 0-1000 0-10000 0-1000 0-1 

01/30/2013 15:05 2.7 12. 95 6.18 20205 1.4 1. 76 0.007 2.00 1. 04 8403.6 110.0 102.: 

Period Average 2.7 12.95 6.52 20276 2.1 3.06 0.007 2.01 1. 59 B433.7 109.4 102.6 

Period Max Value 2.9 12.97 7.16 20414 3.0 4.47 0.008 2.15 2 .23 8525.4 110.0 104. 

Period Min Value 2.' 12.91 6.16 20167 1.4 1. 76 0.007 1. 86 1. 04 8377.2 63.2 101. 

Period Totals = 1.9770E+2 9.4S32E+2 4.7561E+2 1.4801E+6 1.S660E+2 2.2335E+2 5.3700E-l 1. 4669E+2 1.1617E+2 6.1S66E+5 7.9832E+3 7.49S1E+ 

Period % Recovery 64.0 64.0 64.0 64.0 64. a 64.0 64.0 64.0 64.0 64.0 64.0 64. 

Date/Time Printed: 01/31/2013 12,20 2>Summary - I-Min RATA - Continued PagE 
Data Summary Report 

Company: CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 92240 

'JC?i,\.t \ V~"\- 1, 

Source: 9-A~ ~2 Data Group: 

Report Name: 

Start of Report : 

Turbine 2 

2>1-Min Cales 

2>Summary - I-Min RATA 

01/30/2013 13,11 

G12-C4 

t\¥o, \~b- ~p~, eAtt 

End of Report: 01/30/2013 15:05 

Gl2-ell G12-C20 Gl2-C) G12 -C13 G12-CIO 

TRACE 

Environmental Systems, [" c. 

validation: All Available Data 

Group#-Channel# G12-C6 G12-C7 G12-C8 G12-C18 G12 - C 

Long Descrip. 

Short Descrip . 

units 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkFlow 2>Stk CO 2>CD Mass 2>NOx Rate 2>Stk NOXc 2 >Stk CDc 2>Gas Flow 2>NH3 Inj 2>MW La 

Range 

01/30/2013 13:11 

01/30/2013 13:12 

01/30/2013 13:13 

01/30/2013 13:14 

01 /30/2 013 13:15 

01/30/2013 13:16 

01/30/2013 13:17 

01/30/2013 13:18 

01/30/2013 13:19 

01/30/2013 13:20 

01/30/2013 13:21 

01/30/2013 13:22 

01/30/2013 13:23 

01/30/2013 13:24 

01/30/2013 13:25 

01/30/2013 13:26 

01/30/2013 13:27 

01/30/2013 13:28 

01/30/2013 13:29 

01/30/2013 13:30 

01/30/2013 13;3 1 

01/30/2 013 13:32 

01/30/2013 13:33 

01/30/2013 13;34 

01/30/2013 13 :35 

01/30/2013 13:36 

01/30/2013 13:37 

01/30/2013 13:38 

01/30/2013 13 :39 

01/30/2013 13:40 

Date/Time Printed: 

2.8 

2.8 

2.' 

2.8 

2.8 

2.7 

2.8 

2 .. 8 

2.8 

2.8 

2.8 

2.8 

2.7 

2.8 

2.7 

2.8 

2.7 

2.' 

2.' 

2.8 

2.' 

2.' 

2.' 

2.' 

2.8 

2.8 

2 . 8 

2.7 

2.7 

2.8 

Stk 02 

• 

0-25 

12.96 

12.95 

12.94 

12.96 

12.95 

12.96 

12.95 

12.94 

12 . 94 

12.95 

12.96 

12.96 

12.96 

12 .96 

12.96 

12.96 

12.97 

12.94 

12.91 

12.93 

12.93 

12.93 

12.92 

12.92 

12.93 

12.93 

12.94 

12.96 

12.95 

12 . 95 

01/31/2013 12 , 21 

NOx Mass 

Ib/hr 

0 - 100 

7.10 

7.12 

7.13 

7.11 

7.11 

6.22 

7.10 

7.11 

7.09 

7.10 

7. 09 

7.08 

6.20 

7.08 

6.20 

7.08 

6.19 

7.12 

7.16 

7.15 

7.14 

7.15 

7.14 

7.14 

7.15 

7.13 

7.12 

6.21 

6.21 

7.10 

StkFlow 

kscfh 

0-300000 

20356 

20375 

20384 

20366 

20359 

20360 

20309 

20325 

20274 

20327 

20310 

20304 

2 0302 

20288 

20317 

20285 

20308 

20368 

20395 

20400 

20391 

20414 

20370 

20363 

20403 

20361 

20355 

20337 

20320 

20333 

Stk CO 

ppm 

0-1000 

2.5 

2.6 

2.5 

2.6 

2.6 

2.8 

2.6 

2.' 

2.7 

2.7 

2.7 

2.8 

2.8 

2.7 

3.0 

2.7 

2.' 

2.' 

2.6 

2.8 

2.6 

2.6 

2.8 

2 . 5 

2.5 

2.8 

2.6 

2.5 

2.' 

2 .7 

CO Mass 

Ib/hr 

0 - 100 

3.55 

3.56 

3.57 

3.55 

3.56 

4 .44 

3.55 

4.44 

3.55 

3.55 

3.54 

4.43 

4.4 3 

3.54 

4.43 

3.54 

4.4 2 

4.45 

3.58 

4.47 

3.57 

3.58 

4.47 

3.57 

3.57 

4.46 

3.56 

3.55 

4 .44 

3.55 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.008 

0 . 008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0.007 

0.008 

0 . 008 

0.008 

0 . 008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.007 

0.008 

stk NOXc 

ppm 

0-300 

2.08 

2.08 

2.15 

2.08 

2.08 

2.01 

2.08 

2.08 

2.08 

2.08 

2.08 

2.08 

2.01 

2.08 

2.01 

2.08 

2.01 

2.15 

2.14 

2.07 

2.15 

2.15 

2.14 

2.14 

2.07 

2.07 

2.08 

2.01 

2.00 

2.08 

Stk CDc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1.86 8455.8 

1.93 8474.4 

1.85 8488.8 

1.93 8460.0 

1.93 8467.8 

2.08 8457.6 

1.93 8446.8 

2.15 8464 .2 

2.00 8443.2 

2.00 8454.6 

2.01 8436.6 

2 .08 84 34.2 

2.08 8433.6 

2.01 8 4 27.6 

2.23 8439.6 

2.01 8426.4 

2.16 8425.2 

2.15 8482.2 

1.92 8525.4 

2.07 8506.2 

1.92 8502.6 

1 .92 8512.2 

2 . 07 8504.4 

1. 85 8501. 4 

1.85 8507.4 

2.07 8490.0 

1. 93 

1. 86 

2.15 

2.00 

8476.8 

8448.0 

8451.6 

8457.0 

NH3Inj 

Ib/hr 

0-1000 

110. 0 

110 .0 

110. 0 

110.0 

110.0 

110.0 

110 .0 

110.0 

63.2 

110 .0 

110. 0 

110.0 

110.0 

110.0 

110.0 

11.0.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

1 10.0 

MW Lo 

0-1 

103 .. 

103.: 

103 .. 

103.1 

103. : 

102. 

102 . . 

103. : 

102 .. 

102 

103. 1 

102 .. 

102 .. 

102 . . 

102 .. 

102.! 

102 . . 

103. 

104 

103 ' 

103.' 

103.' 

103. 

103.' 

103. 

103.! 

103." 

102.: 

103.: 

102.' 

Pag( 
Group# - Channel# 

Long Descri p . 

Short Des crip. 

Un i ts 

Range 

01/30/2013 13:41 

01/30/2013 13:42 

01/30/2013 13:43 

01/30/2013 13:44 

01/30/2013 13:45 

01/30/2013 13:46 

01/30/2013 13:47 

01/30/2013 13:48 

01/30/2013 13:49 

01/30/2013 13:50 

01/30/2013 13:51 

01/30/2013 13:52 

01/30/2013 13:53 

01/30/2013 13:54 

01/30/2013 13:55 

01/30/2013 13:56 

01/30/2013 13:57 

01/30/2013 13:58 

01/30/2013 13:59 

01/30/2013 14:00 

01/30/2013 14:01 

01/30/2013 14:02 

01/30/2013 14:03 

01/30/2013 14:04 

01/30/2013 14:05 

01/30/2013 14:06 

01/30/2013 14:07 

01/30/2013 14:08 

01/30/2013 14:09 

01/30/2013 14:10 

01/30/2013 14:11 

01/30/2013 14:12 

01/30/2013 14:13 

01/30/2013 14:14 

01/30/2013 14:15 

01/30/2013 14:16 

01/30/2013 14:17 

01/30/2013 14:18 

01/30/2013 14:19 

01/30/2013 14:20 

Date/Time Printed: 

G12-C2 G12 -C4 G12 -C11 G12-C20 

2>Stk NOx 

Stk NOx 

2 >Stk 02 2 :>NOx Mass 2 >StkFlow 

ppm 

0-150 

2.B 

2.7 

2.7 

2.7 

2 .B 

44.4 B 

61. a B 

60.1 B 

21.1 B 

1.3 B 

6.9 B 

16.1 B 

51.3 B 

57.0 B 

54.5 B 

56.1 B 

56.8 B 

57 .0 B 

57.1 B 

57.3 B 

57.1 B 

57.2 B 

57.6 B 

57.48 

57.78 

57.48 

42.78 

3.88 

2 .9 8 

L18 

2.88 

3.28 

2.48 

2.3 B 

2.2 B 

2.2 B 

2.1 B 

2.38 

2.2 B 

2.28 

stk 02 

• 

0-25 

12.95 

12.96 

12.95 

12.95 

12.95 

13.278 

13.348 

13.38 B 

14.11 B 

15.878 

15.618 

14.54 B 

13.85 B 

13.80 B 

13.838 

13.808 

13.808 

13.80 B 

13.79 B 

13 .78 B 

13.78 B 

13.77B 

13.768 

13.76 B 

13.75 B 

13.77 B 

14.078 

15.138 

15.64 B 

15.23 B 

14. 07 8 

13.38 B 

13 .30 B 

13.318 

13.328 

13.31 B 

13.328 

13.298 

13.23 B 

12.96 B 

01/31/2013 12,21 

NOx Mass 

Ib/hr 

0-100 

7.09 

6.20 

6.20 

6.20 

7.10 

100.008 

100.00B 

100.00B 

34.41B 

1. 65 8 

10.59 B 

33. 04 B 

100.00B 

100.00B 

100 .00B 

100.00B 

100. 00 B 

100.00 B 

100.00B 

100.008 

100. 00 8 

100.008 

100 . 00B 

100.00B 

100.00B 

100 . 00 B 

87.358 

5.09 B 

3.858 

1.66 B 

5.908 

7.85 B 

6.19 B 

6 .19 B 

5.31 B 

5.31 B 

5.31 B 

6.21 B 

5.318 

5.318 

StkFlow 

kscfh 

0-300000 

20306 

20301 

20293 

20270 

20332 

193398 

200908 

19248 B 

135688 

9923 B 

13012 B 

171948 

198358 

20470 B 

200468 

204838 

20483 B 

205648 

20459 B 

204848 

204248 

204928 

20434 B 

204028 

204228 

203658 

171198 

11462 B 

111098 

133258 

174708 

21125 B 

211888 

211998 

21235 B 

212428 

212618 

21234 B 

209868 

202888 

G12-C3 G12 -C13 G12-C10 G12-C6 G12 - C7 G12 -C8 G12 -C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2 >Stk NOXc 2>Stk COc 2>Gas Flow 2 >NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

2.7 

2.7 

2.9 

2 . B 

3.0 

1. 58 

0.08 

0.08 

0.08 

0.08 

0.0 B 

0.0 B 

o. a 8 

0.0 B 

0.08 

0.08 

0.08 

0.0 B 

0.0 B 

0.08 

0.08 

0.0 B 

0.08 

0.0 B 

0.08 

0.08 

0.0 B 

O. a 8 

0.08 

0.08 

0.4 B 

2.6 B 

4.38 

3.9 B 

3.2 B 

2.8 B 

3.08 

2.68 

2 . 48 

2.6 B 

CO Mass 

Ib/hr 

0-100 

3.55 

3.54 

4.43 

4.43 

4.44 

2.438 

0.008 

O. 00 8 

0.00 B 

0.00 B 

0.00 B 

O. 00 8 

0.008 

O. 00 B 

0.00 B 

0.008 

0.008 

0.00 B 

0.008 

0.00 B 

0.00 B 

0.008 

0.00 B 

0.008 

0.00 B 

0.008 

0.008 

0.00 B 

0.00 B 

0.00 B 

0.66 B 

4.36 B 

6.19 B 

6.19 B 

5.318 

4.438 

4.438 

4.44 B 

3.54 B 

3.54 B 

NOx Rate 

Ib/mmBt.u 

0-1 

O.OOB 

0.007 

0.007 

0.007 

0 .008 

0.126 B 

0.175 B 

0.174 B 

0.068 B 

0.0068 

0.0288 

0.055B 

0.1588 

0.174 B 

0.168 B 

0.1728 

0.1748 

0.174 B 

0.1758 

0.1758 

0.1748 

0.1748 

0.1758 

0.175 B 

0.1758 

0.175 B 

0.1368 

0.014 8 

0.0128 

0.004 B 

0.009 B 

0.009 B 

0.007 B 

0.007 B 

0.006 B 

0.0068 

0.0068 

0.007 B 

0.006 B 

O. 006 8 

stk NOXe 

ppm 

0 -300 

2. 08 

2.01 

2.00 

2.00 

2.08 

34.338 

47.61B 

47.15 B 

18.33B 

1. 52 B 

7.70 B 

14.94 B 

42.93 B 

47.37B 

45.488 

46.628 

47.208 

47.37 B 

47.388 

47.488 

47.328 

47.338 

47.60 B 

47 . 438 

47.618 

47.508 

36.898 

3.898 

3.258 

1 .148 

2.428 

2.51 B 

1.868 

1.79 B 

1. 71 8 

1.71 B 

1. 63 B 

1.78 B 

1. 69 8 

1. 63 B 

Stk COe Gas hscfh 

ppm hsefh 

0-1000 0-10000 

2.00 8445.6 

2.01 8433.0 

2.15 8440.2 

2.08 8430.6 

2.23 8456.4 

1.168 7719.68 

O . OOB 7945.8B 

0.008 

O . 00 B 

0.00 B 

0.00 B 

0.00 B 

O. 00 8 

0.00 B 

0.008 

0.008 

0.00 B 

0.008 

0 . 00 B 

0.008 

0.008 

0.008 

0.00 B 

0.00 B 

0.008 

0.008 

0.00 B 

0.00 B 

0.008 

0.00 B 

0.35 B 

2.04 B 

3.34 B 

3.03 B 

2.498 

2.18 B 

2.34 B 

2.028 

1.858 

1.93 B 

7572.6B 

4819.88 

2611.28 

3601.2B 

5721.0B 

7315.88 

7603.88 

7414.88 

7608.6 B 

7608.68 

7638.6B 

7610.48 

7630.2B 

7608.08 

7644.08 

7633.28 

7621.28 

7639.28 

7596.6B 

6117.0B 

3460.2B 

3057.08 

3952.88 

6242.4B 

8311.2 B 

8424.68 

8418.08 

8421.08 

8434.8B 

8431.28 

8454.08 

8421.0B 

8427.6 B 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 B 

110.08 

110.08 

110.08 

110.0 B 

110.08 

110.0 B 

110.0 B 

110.0 B 

110.0 B 

110.0 B 

110. 08 

110 .0 B 

110.08 

110.08 

110.0 B 

110.08 

110.08 

110.0 B 

110.08 

110.08 

110 .0 B 

110.08 

110 .0 B 

110.0 B 

110.0 B 

110. a 8 

110.0 B 

110.08 

110.08 

110.08 

110.0 B 

110.0 B 

110.08 

110.0 B 

2>Summary - I-Min RATA - Continued 

MW Lo 

0-1 

103 . . 

103. ( 

102. 

103. ! 

102. 

92 . . 

9B 

90 .. 

45. 

16 .. 

32.: 

65.' 

89.! 

93. ( 

89 . . 

92 

92 .. 

92. ; 

93. ( 

93 .. 

92. 

93 . . 

93 .. 

92. : 

93. : 

92 . ~ 

66.1 

25.' 

22 .. 

36.( 

71.: 

101. : 

102. 

102. ( 

102. : 

102. : 

102 _ 

102. 

102. ( 

102. 

PagE 
Gro up#-Channel# 

Long Descri p. 

Short Descrip. 

Uni ts 

Range 

01/30/2013 14:21 

01/30/2013 14:22 

01/30/2013 14:23 

01/30/2013 14:24 

01/30/2013 14:25 

01/30/2013 14:26 

01/30/2013 14:27 

01/30/2013 14:28 

01/30/2013 14:29 

01/30/2013 14:30 

01/30/2013 14:31 

01/30/2013 14:32 

01/30/2013 14:33 

01/30/2013 14:34 

01/30/2013 14:35 

01/30/2013 14:36 

01/30/2013 14:37 

01/30/2013 14:38 

01/30/2013 14:39 

01/30/2013 14:40 

01/30/2013 14,41 

01/30/2013 14:42 

01/30/2013 14:43 

01/30/2013 14:44 

01/30/2013 14:45 

01/30/2013 14:46 

01/30/2013 14:47 

01/30/2013 14:48 

01/30/2013 14:49 

01/30/2013 14:50 

01/30/2013 14:51 

01/30/2013 14:52 

01/30/2013 14:53 

01/30/2013 14:54 

01/30/2013 14:55 

01/30/2013 14:56 

01/30/2013 14:57 

01/30/2013 14:58 

01/30/2013 14:59 

01/30/2013 15:00 

Date/Time Printed: 

G12-C2 G12-C4 G12-CII G12 -C20 

2>Stk NDx 

Stk NDx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2. 4 B 

2.4 B 

2.5 B 

2.4 B 

2.5 B 

2.5 B 

2.5 B 

2.5 

2.6 

2.5 

2.6 

2.6 

2.6 

2.7 

2.5 

2 . 6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

Stk 02 

• 

0 - 25 

12.94 B 

12.96 B 

12.94 B 

12.96 B 

12.96 B 

12.96 B 

12.96 B 

12.95 

12.95 

12.95 

12.95 

12.94 

12.96 

12.95 

12.97 

12.96 

12.96 

12.96 

12.97 

12.96 

12.96 

12.95 

12.95 

12.96 

12.95 

12.94 

12.94 

12.95 

12.95 

12.94 

12.95 

12.95 

12.95 

12.95 

12 . 96 

12.94 

12.95 

12.95 

12.96 

12.96 

01/31/2013 12,21 

NDx Mass 

Ib/hr 

0-100 

6.20 B 

6.19 B 

6.21 B 

6.19 B 

6.19 B 

6.19 B 

6.19 B 

6.20 

6.19 

6.19 

6.19 

6.18 

6.18 

6.16 

6.17 

6.17 

6.17 

6.17 

6.17 

6.17 

6.18 

6.18 

6.18 

6.18 

6.18 

6.19 

6.19 

6.18 

6.18 

6.19 

6.17 

6.19 

6.19 

6.18 

6.18 

6.18 

6.18 

6.18 

6.16 

6.17 

StkFlow 

kscfh 

0-300000 

20251 B 

2027 3 B 

20280 B 

20282 B 

20282 B 

20258 B 

20284 B 

20288 

20238 

20261 

20234 

20205 

20232 

20167 

202 25 

20210 

20206 

20207 

20224 

20197 

20249 

20228 

20231 

20237 

20231 

20210 

20212 

20218 

20215 

20218 

20197 

20261 

20254 

20215 

20243 

20201 

20222 

20203 

20167 

20197 

G12-C3 G12-C13 G12 -C10 G12-C6 G12 -C7 G12-C8 G12-C18 GI2-C 

2>stk CO 2>CD Mass 2>NOx Rate 2>Stk NDXc 2>Stk CDc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

2,4 B 

2.2 B 

2.3 B 

2.2 B 

2.1 B 

1. 9 B 

1. 9 B 

2.0 

1.. 

1.. 

2.0 

1.9 

1.9 

1.8 

1.8 

1.6 

1.6 

1.7 

1.7 

1.5 

1.6 

1.5 

1.6 

1.4 

1.5 

1.5 

1.5 

1.6 

1.7 

1.7 

1.5 

1.7 

1.5 

1.4 

1.6 

1.5 

1.6 

1.6 

1.5 

1.5 

CO Mass 

1b/hr 

0-100 

3.54 B 

3,54 B 

3.55 B 

3.54 B 

2.65 B 

2.65 B 

2.65 B 

2.66 

2.65 

2,65 

2.65 

2,65 

2.65 

2.64 

2,64 

2,64 

2.64 

2.64 

2.64 

1. 76 

2.65 

1. 77 

2.65 

1. 77 

1. 77 

1. 77 

1. 77 

2.65 

2.65 

2.65 

1. 76 

2,65 

1. 77 

1. 77 

2.65 

1. 77 

2.65 

2.65 

1. 76 

1. 76 

NDx Rate 

Ib/mmBtu 

0-1 

0.007B 

0.007 B 

0,007 B 

0.007 B 

0.007 B 

0.007 B 

0.007 B 

0,007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0,007 

0,007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0,007 

0.007 

0,007 

0.007 

0.007 

0.007 

0.007 

0.007 

0,007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0,007 

0.007 

Stk NDXc 

ppm 

0-300 

1. 78 B 

1. 78 B 

1. 85 B 

1.78 B 

1.86 B 

1,86 B 

1. 86 B 

1. 86 

1. 93 

1. 86 

1. 93 

1. 93 

1. 93 

2.00 

1. 86 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

1. 93 

2.00 

2.00 

1. 93 

2.00 

2.00 

2.00 

1. 93 

2.00 

2.00 

2.00 

1. 93 

2.01 

Stk CDC Gas 

ppm 

0-1000 

1. 78 B 

1.63 B 

1.70 B 

1. 63 B 

1.56 B 

1.41 B 

1.41 B 

1.48 

1.41 

1.41 

1.48 

1.41 

1.41 

1. 34 

1. 34 

1.19 

1.19 

1. 26 

1.26 

1.11 

1.19 

1.11 

1.19 

1. 04 

1.11 

1.11 

1.11 

1.19 

1. 26 

1.26 

1.11 

1. 26 

1.11 

1. 04 

1.19 

1.11 

1.19 

1.19 

1.11 

1.11 

hscfh 

hscfh 

0-10000 

8433 .6 B 

8421. 6 B 

8445,68 

8425.2B 

8425.2B 

8415.0 B 

8425.88 

8438.4 

8417.4 

8427.0 

8415.6 

8414.4 

8404.2 

8388.0 

8391.0 

8395,2 

8393.4 

8394.0 

8390.4 

8389.8 

8411.4 

8413.2 

8414.4 

8406.6 

8414.4 

8416 .2 

8417.4 

8409 .0 

8407.8 

8419.8 

8400.6 

8427.0 

8424.0 

8407.8 

8409.0 

8412.6 

8410 ,8 

8403.0 

8377.2 

8389.8 

NH3Inj 

1b/hr 

0-1000 

110.0 B 

110.0 B 

110, a B 

110, a B 

110,0 B 

110. a B 

110. a B 

110,0 

110.0 

110,0 

110.0 

110.0 

110.0 

110 ,0 

110,0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110,0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110,0 

110.0 

110.0 

2>Summary - 1-Min RATA - Continued 

MW Lo 

0 - 1 

102, : 

102 .. 

1 02 .. 

102 .. 

102. 

102. ! 

102. ' 

103.: 

102. 

102 

102 

102 

102. : 

101.: 

102 .. 

102 .1 

102. : 

101,: 

101 .. 

102, I 

102. : 

102 

102. : 

102. 

102 

102. 

102. : 

102 . . 

102.! 

102.1 

102.1 

102.! 

102 .. 

102. 

102. ! 

102 . . 

102. 

102. : 

102. : 

102. : 

Pag( 
Group#-Channel# 

Long Descrip. 

Short Descrip. 

Units 

Range 

01/30/2013 15:01 

01/30/2013 15:02 

01/30/2013 15:03 

01/30/2013 15:04 

01/30/2013 15:05 

Period Average 

Period Max Value ~ 

Period Min Value -

Period Totals -

Period % Recovery 

Dat e /Time Printed: 

G12 - C2 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2.6 

2.7 

2.6 

2.7 

2.7 

G1 2 -C4 G12 - Cl1 G12-C20 

2>Stk 02 2>NOx Mass 2>StkFlow 

Stk 02 

• 

0-25 

12.95 

12.95 

12.95 

12.95 

12.95 

NOx Mass 

Ib/hr 

0-100 

6.17 

6.17 

6.17 

6.18 

6.18 

StkFlaw 

kscfh 

0 - 300000 

20180 

20186 

20189 

20225 

20205 

G12 -C3 G12 -Cl3 GI2 - CIO G12-C6 G12-C7 G12-CB G12-C1B G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW La 

Stk CO 

ppm 

0-1000 

1.6 

1.4 

1.5 

1.4 

1.4 

CO Mass 

Ib/hr 

0-100 

2.64 

1.76 

1. 76 

1. 77 

1. 76 

NOx Rate 

Ib/mmBtu 

0 - 1 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1.93 

2.00 

1.93 

2.00 

2.00 

Stk CDc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1.19 8393.4 

1.04 8395.8 

1.11 B397.0 

1.04 

1.04 

8412.0 

8403.6 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110 . 0 

110.0 

110.0 

MW Lo 

0-1 

102.: 

102.( 

102.1 

102. 

102.: 

11.2 13.24 21.35 19826 1.7 2.53 0.034 9.14 1.30 7994.7 109.6 96.4 

61.0 15. 8 7 100.00 21261 4 .3 6.19 0.175 4 7.61 3.3 4 8525.4 110.0 104. 

1. 1 12. 91 1.65 9923 0.0 0 .00 0.004 1.14 0 .00 2611.2 63.2 16. 

1.2917E+) 1.5227E+3 2. 4 S5SE+3 2.2800E+6 2.0090E+2 2 . 9 099E+2 3.8710E+O 1.0515E+3 1.5002E+2 9.1938E+5 1.2603E+4 1.1090E+ 

100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100 . 0 100.0 100.0 100. 

01/31/2013 12,21 2>Summary - I-Min RATA - Continued PagE 
Appendix B.1.3 Sentinel Unit 2 PM Testing 

R0410673 8-5 blta.!d 
Data Summary Report 

Company : CPV SentineL LLC 

62575 Powerline Road 

Desert Hot Springs, CA 92240 

Source : Turbine 2 

Data Group : 

Report Name: 

SuJ\.uA tJ ,,',1- Z. pM TRACE ~_ llq\\L - ~M- ~- \ Enr';roflmeflla l Sy sl ellls, Iflc. 

Start of Report: 

2:>1-Min Cales 

2>Summary - l-Min RATA 

02/01/2013 14,14 End of Report, 02/01/2013 18,25 Validation: All Available Data 

Group#-Channe l# 

Lo ng Descrip. 

Short Descrip . 

Units 

Range 

02/01/2013 14:14 

02/01/2013 14:15 

02/01/2013 14:16 

02/01/2013 14:17 

02/01/2013 14:18 

02/01/2013 14:19 

02/01/2013 14:20 

02/01/2013 14:21 

02/01/2013 14:22 

02/01/2013 14:23 

02/01/2013 14:24 

02/01/2013 14:25 

02/01/2013 14:26 

02/01/2013 14:27 

02/01/2013 14:28 

02/01/2013 14:29 

02/01/2013 14:30 

02/01/2013 14:31 

02/01/2013 14:32 

02/01/2013 14:33 

02/01/ 2 013 14:34 

02/01/2013 14:35 

02/01/2013 14:36 

02/01/2013 14:37 

02/01/201 3 14:38 

02/01/2013 14:39 

02/01/2013 14:40 

02/01/2013 14:41 

02/01/2013 1 4 :42 

02/01/ 2 013 14:43 

Date/Time Printed: 

G12-C2 G12-C4 Gl2 -CII 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

1., 

1.. 

1.. 

1.8 

1.8 

2.0 

2.0 

1.. 

1.8 

1.. 

1.' 

1.. 

1.8 

1.' 

1.. 

1.' 

1.8 

2.2 1., 

2.1 

2.2 

2.2 

2.1 

2.0 

2.1 

2.1 

2.0 

2.0 

2.0 

2.0 

Stk 02 

• 

0-25 

14.37 

14.35 

14.35 

14.37 

14.36 

14. 3 4 

14.34 

14.36 

14 .36 

14.36 

14.35 

14.35 

14.36 

14 .36 

14 . 37 

14.36 

14.36 

14.34 

14 . 37 

14 . 3 4 

14.34 

14.33 

14.35 

14.34 

14.34 

14.34 

14.35 

14.35 

14.35 

14.35 

02/02/2013 12 , 40 

NOx Mass 

lb/hr 

0-100 

3.35 

3.36 

3.36 

3.36 

3.37 

3.93 

3.93 

3.35 

3.36 

3.35 

3.36 

3.35 

3.35 

3.35 

3.36 

3.36 

3.35 

3.91 

3.35 

3.91 

3.90 

3.91 

3.91 

3.91 

3.92 

3.93 

3.92 

3.92 

3.92 

3.92 

G12-CZO 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

15585 

15578 

15576 

15589 

15617 

15563 

15572 

15558 

15588 

15561 

15553 

15532 

15542 

15560 

15601 

15586 

15535 

15509 

15541 

15510 

15477 

15489 

15517 

15514 

15558 

15570 

15576 

15546 

15564 

15571 

GI2-C) 

2>Stk CO 

Stk co 

ppm 

0 - 1000 

0.3 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.3 

GI2-CD Gl2-ClO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

lb/hr 

0-100 

0.56 

0.00 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.56 

0.56 

NOx Rate 

Ib/mmBtu 

0-1 

0.006 

0.006 

0.006 

0.006 

0.00 6 

0.007 

0.007 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.006 

0.007 

0.006 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 72 

1. 71 

1. 71 

1. 63 

1. 62 

1. 80 

1. 80 

1. 71 

1. 62 

1. 71 

1. 71 

1. 71 

1. 62 

1. 71 

1. 72 

1. 71 

1.62 

1. 98 

1. 72 

1. 89 

1. 98 

1. 98 

1. 89 

1. 80 

1. 89 

1. 89 

1. 80 

1. 80 

1. 80 

1. 80 

G12-C7 G12-C8 

2>Stk CDc 2>Gas Flow 

Stk CDc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

0.27 

0.18 

0.18 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.18 

0 . 27 

0.27 

5324.4 

5338.2 

5337.6 

5325.6 

5343.6 

5341.2 

5344.2 

5323.2 

5333.4 

5324.4 

5329.8 

5322.6 

5317.8 

5323.8 

5329.8 

5332.8 

5315.4 

5322.6 

5309.4 

5323.2 

5311.8 

5323.8 

5317.2 

5324.4 

5339.4 

5343.6 

5337.6 

5327.4 

5333.4 

5335.8 

GI2-C1S 

2>NH3 Inj 

NH3Inj 

lb/hr 

0-1000 

107.3 

107.2 

108.7 

108.8 

109.0 

106.0 

106.8 

107.0 

106.7 

107.0 

107.2 

107.7 

107.2 

106.5 

106.3 

107.3 

105.7 

104.7 

106.5 

105.2 

104.0 

104.5 

106.0 

107.0 

105.7 

106.3 

105.8 

106.3 

106.7 

106.8 

G12-C 

2>MW Lo 

MW Lo 

0-1 

54 . . 

54 ' 

54.' 

54.: 

55.1 

54.: 

54.: 

54.' 

54.' 

54.' 

54.' 

54.: 

54 .: 

54 . ! 

54.: 

54.: 

54 

54. 

54. ' 

54.' 

54 . 1 

54.: 

54 

54. 

54 .. 

54. 

54 .. 

54. : 

55.1 

55.1 

PagE 
Gro up# - Channel# 

Long Desc rip. 

Short De s crip . 

units 

Range 

02/01/2013 14:44 

02/01/2013 14:45 

02/01/2013 14:46 

02/01/2013 14:47 

02/01/2013 14:48 

02/01/2013 14:49 

02/01/2013 14:50 

02/01/2013 14:51 

02/01/2013 14:52 

02/01/2013 14:53 

02/01/2013 14:54 

02/01/2013 14:55 

02/01/2013 14:56 

02/01/2013 14:57 

02/01/2013 14:58 

02/01/2013 14:59 

02/01/2013 15:00 

02/01/2013 15:01 

02/01/2013 15:02 

02/01/2013 15:03 

02/01/2013 15:04 

02/01/2013 15:05 

02/01/2013 15:06 

02/01/2013 15:07 

02/01/2013 15:08 

02/01/2013 15:09 

02/01/2013 15:10 

02/01/2013 15:11 

02/01/2013 15:12 

02/01/2013 15:13 

02/01/2013 15:14 

02/01/2013 15:15 

02/01/2013 15:16 

02/01/2013 15:17 

02/01/2013 15:1S 

02/01/2013 15:19 

02/01/2013 15:20 

02/01/2013 15:21 

02/01/2013 15:22 

02/01/2013 15:23 

Date/Time Printed: 

G12-C2 G12-C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

2>Stk 02 2>NOx Mass 2>StkFlow 

ppm 

0-150 

1.. 

2.0 

2 . 1 

2.0 

2.2 

2.2 

2.1 

2.1 

2.2 

2.1 

1.. 

2.1 

2 . 1 

2.1 

2.2 

2.1 

2 . 2 

2.1 

2.1 

2.1 

2.0 

2.0 

2.0 

2.0 

2.2 

2.2 

2.1 

2.1 

2.1 

2.2 

2.0 

2.1 

2.2 

2.0 

2.1 

2.1 

2.2 

2.2 

2.2 

2.2 

Stk 02 

• 

0-25 

14.36 

14.35 

14.34 

14 .34 

14.32 

14.32 

14.33 

14.33 

14.33 

14.34 

14 .35 

14.33 

14 .32 

14 .32 

14.32 

14.33 

14 . 32 

1 4 .32 

14.31 

14.33 

14.33 

14 .34 

14 .34 

14.34 

14.32 

14.33 

14.33 

14.34 

14.33 

14 . 30 

14.31 

14.32 

14 .32 

14.34 

14 .31 

14.32 

14.31 

14.31 

14.31 

14.31 

02/02/2013 12,40 

NOx Mass 

1b/hr 

0-100 

3.35 

3.92 

3.93 

3.92 

3.93 

3.93 

3.94 

3.94 

3.94 

3.94 

3.38 

3.95 

3.94 

3.95 

3.94 

3.94 

3.94 

3.94 

3.95 

3.94 

3.94 

3.94 

3.93 

3.92 

3.94 

3.94 

3.93 

3.93 

3.94 

3.95 

3.96 

3.95 

3.97 

3.96 

3.98 

3.98 

3.99 

3.98 

3.98 

3.98 

StkFlow 

kscfh 

0 -3 00000 

15556 

15571 

15570 

15554 

15540 

15536 

15586 

15586 

15579 

15605 

15637 

15625 

15582 

15620 

15585 

15600 

15568 

15577 

15596 

15583 

15595 

15605 

15596 

15554 

15580 

15590 

15569 

15584 

15586 

15564 

15617 

15601 

15688 

156S9 

15697 

15711 

15725 

15703 

15711 

15722 

G12-C3 G12-C13 G12-C10 G12-C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW La 

Stk CO 

ppm 

0-1000 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.3 

0.2 

0.2 

0.2 

0.2 

0.3 

CO Mass 

1b/hr 

0-100 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.S6 

0.56 

0.57 

0.56 

0.00 

0.00 

0.57 

0.00 

0.00 

0.00 

0.00 

0.57 

NOx Rate 

lb/mmBtu 

0-1 

0.006 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.006 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 71 

1. 80 

1. 89 

1. 80 

1. 97 

1. 97 

1. 89 

1. 89 

1. 98 

1. 89 

1. 71 

1. 89 

1. 88 

1. 88 

1. 97 

1. 89 

1. 97 

1. 88 

1. 88 

1. 89 

1. 80 

1. 80 

1. 80 

1. 80 

1. 97 

1. 98 

1. 89 

1. 89 

1. 89 

1. 97 

1. 79 

1. 88 

1. 97 

1. 80 

1. 88 

1. 88 

1. 97 

1. 97 

1. 97 

1. 97 

Stk COc Gas 

ppm 

hscfh 

hscfh 

0-1000 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0.27 

0.18 

0.18 

O.lS 

0.18 

0.27 

0-10000 

5322.6 

5335.8 

5343.6 

5338.2 

5349.6 

5348.4 

5357.4 

5357 .4 

5355.0 

5355.6 

5358.6 

5370 . 6 

5364.0 

5377 . 2 

5365.2 

5362.2 

5359.2 

5362.2 

5377.2 

5356.2 

5360.4 

5355.6 

5352.6 

5338.2 

5363.4 

5358.6 

5351.4 

5348 . 4 

5357.4 

5374.2 

5384.4 

5370.6 

5400.6 

5384 .4 

5412.0 

5408.4 

5421.6 

5413.8 

5416 . 8 

5420.4 

NH3Inj 

lb/hr 

0-1000 

107.7 

107.0 

106.2 

107.0 

107.0 

106.8 

105.2 

105.8 

105.7 

107.3 

107.3 

106 . 0 

106.5 

106.3 

106.7 

106 . 7 

106.8 

106 . 8 

107.2 

107.5 

107.5 

106.8 

107 . 2 

106.2 

10S.7 

10S.8 

107.2 

104.3 

106.0 

107 . 0 

106.7 

107.2 

107.3 

109.0 

108.8 

107.8 

107.5 

108.2 

107.8 

108.8 

2>Summary - I-Min RATA - Continued 

MW La 

0-1 

54 .. 

55. ! 

54. 

54 

55.1 

55 . ! 

55. ! 

S5. ! 

54. : 

55. ! 

54. 

55. ! 

55. : 

55. : 

55 . • 

55. ! 

54. : 

55. : 

55. : 

54. : 

55.: 

54. : 

55. ! 

54. : 

55. : 

55.1 

54. : 

55. ! 

55. : 

55 .. 

55. ! 

55. 

55.1 

55. 

56. ! 

55 .. 

56. : 

56.1 

55. ' 

56 .• 

pagt 
Group#-Channel# 

Long Descrip. 

Short Descri p. 

Units 

Range 

02/01/2013 15:24 

02/01/2013 15:25 

02/01/2013 15:26 

02/01/2013 15:27 

02/01/2013 15:28 

02/01/2013 15:29 

02/01/2013 15:30 

02/01/2013 15:31 

02/0 1 /2013 15:32 

02/01/2013 15:33 

02/0l/20l3 15:34 

02/01/2013 15:35 

02/01/2013 15;36 

02/01/2013 15;)7 

02/01/2013 15;38 

02/01/2013 15;)9 

02/01/2013 15;40 

02/01/2013 15:41 

02/01/2013 15:42 

02/01/2013 15:43 

02/01/2013 15;44 

02/01/2013 15:45 

02/01/2013 15:46 

02/01/2013 15:47 

02/01/2013 15:48 

02/01/2013 15:49 

02/01/2013 15;50 

02/01/2013 15;51 

02/01/2013 15:52 

02/01/2013 15:53 

02/01/2013 15:54 

02/01/2013 15:55 

02/01/2013 15:56 

02/01/2013 15:57 

02/01/2013 15:58 

02/01/2013 15;59 

02/01/2013 16;00 

02/01/2013 16:01 

02/01/2013 16:02 

02/01/2013 16:03 

Date/Time Printed: 

G12-C2 G12 -C4 G12 - C11 G12-C20 

2,Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2~NOx Mass 2>StkFlow 

2.1 

2.0 

2.1 

2.1 

2.1 

2.2 

2.1 

2.0 

2.1 

2.1 

2.0 

2.0 

2.0 

2.0 

2.2 

2.0 

2.1 

2.0 

2.0 

2.0 

2.0 

2.1 

2.1 

2.0 

2.0 

2.2 

2.0 

2.1 

2.1 

2.3 

2.0 

2.2 

2.1 

2.0 

2.1 

2.1 

2.1 

2.2 

2.2 

2.3 

Stk 02 

• 

0.-25 

14.32 

14.32 

14.30 

14 .31 

14.31 

14.31 

14.32 

14.32 

14.32 

14.33 

14.32 

14 .32 

14 .32 

14.32 

14 . 32 

14.32 

14.33 

14.32 

14.33 

14.34 

14 .33 

14.34 

14 . 34 

14.34 

1 4 .34 

14.33 

14.32 

14.31 

14.32 

14 .31 

14 .31 

14.31 

14 . 34 

14.34 

14.34 

14.35 

14.34 

14.33 

14.3 2 

14.32 

02/02/2013 12:40 

NOx Mass 

lb/hr 

0-100 

3.98 

3.97 

3.98 

3.98 

3.98 

3.99 

3.98 

3.97 

3.98 

3.96 

3.97 

3.97 

3.95 

3.96 

3.95 

3.95 

3.95 

3.94 

3.95 

3.94 

3.94 

3.94 

3.93 

3.94 

3.93 

3.93 

3.95 

3.95 

3.95 

4.52 

3.95 

3.96 

3.93 

3.92 

3.92 

3.92 

3.93 

3.93 

3.94 

4.51 

StkFlow 

kscfh 

0-300000 

15723 

15707 

15689 

15694 

15722 

15736 

15726 

15681 

15733 

15658 

15678 

15674 

15625 

15636 

15610 

15615 

15630 

15590 

15625 

15617 

15583 

15607 

15600 

15626 

15591 

15562 

15603 

15603 

15610 

15612 

15603 

15647 

15586 

15559 

15549 

15560 

15561 

15564 

15580 

15584 

G12 - C3 GI2-C13 G12-CIO G12-C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW La 

Stk CO 

ppm 

0-1000 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

CO Mass 

lb/hr 

0-100 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.00 

0.57 

0.00 

0.57 

0.57 

0.57 

0.56 

0.57 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.57 

0.56 

0.57 

0.56 

0.00 

0.00 

0.56 

0.56 

0 . 56 

0 . 56 

0.56 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

Stk NOXc 

ppm 

0 - 300 

1. 88 

1. 79 

1. 88 

1. 88 

1. 88 

1. 97 

1. 88 

1. 79 

1. BB 

1. 89 

1. 79 

1. 79 

1. 79 

1. 79 

1. 97 

1. 79 

1. 89 

1. 79 

1.80 

1. 80 

1. BO 

1. 89 

1. 89 

1. 80 

1. 80 

1. 9B 

1. 79 

1.88 

1. 88 

2.06 

1. 79 

1. 97 

1. 89 

1. 80 

1.89 

1. 89 

1. 89 

1. 9B 

1. 97 

2.06 

Stk COc Gas 

ppm 

hscfh 

hscfh 

0-1000 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.27 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0 . 27 

0 . 27 

0.27 

0.18 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0 - 10000 

5412.6 

5407.2 

5417.4 

5410.8 

5420.4 

5425.2 

5413.8 

5398.2 

5416.2 

5382.0 

5397.0 

5395.8 

5379.0 

5382.6 

5373.6 

5375.4 

5372.4 

5367.0 

5370.6 

5359.8 

5356.2 

5356.2 

5353.8 

5362.B 

5350.8 

5349.0 

5371. 2 

5379.6 

5373.6 

5382.6 

5379.6 

5394.6 

5349.0 

5340.0 

5336.4 

5332.2 

5340.6 

5349.6 

5363.4 

5364.6 

NH3Inj 

lb/hr 

0-1000 

108.3 

108.3 

108.7 

107.8 

106.8 

107.8 

109.3 

108.5 

108 . 5 

107.3 

108.5 

108.0 

108.5 

106.7 

106.0 

106.5 

106.7 

107.5 

106.5 

107.2 

107.5 

107.2 

107.3 

107.5 

105.8 

105.8 

107.3 

106.3 

106.7 

106.7 

106.3 

105.8 

106.3 

106.8 

105.7 

106.0 

105.3 

105.3 

105.3 

106.2 

2>Summary - I-Min RATA - Continued 

MW La 

0-1 

56.1 

55 .. 

S5. : 

56.1 

56 . . 

55. 

55. 

55.l 

5S. : 

S5 .. 

55. : 

55 .. 

SS .: 

55.: 

55 . ~ 

5S. : 

55 .. 

55. : 

55.: 

5S .: 

55.: 

54. : 

55.1 

55.1 

54. ; 

55.1 

55 .. 

55.: 

5S.1 

5S. : 

55 . . 

55. 

54.: 

54.· 

54.: 

54.: 

54.: 

54.: 

55. 

55.· 

Pagt 
Gro up#- Channel# 

Long Des c r i p . 

Short Des cri p . 

Un its 

Range 

02/01/2013 16;04 

02/01/2013 16;05 

02/01/2013 16;06 

02/01/2013 16;07 

02/01/2013 16;08 

02/01/2013 16:09 

02/01/2013 16:10 

02/01/2013 16:11 

02/01/2013 16:12 

02/01/2013 16:13 

02/01/2013 16:14 

02/01/2013 16:15 

02/01/2013 16:16 

02/01/2013 16:17 

02/01/2013 16:18 

02/01/2013 16:19 

02/01/2013 16:20 

02/01/2013 16:21 

02/01/2013 16:22 

02/01/2013 16:23 

02/01/2013 16:24 

02/01/2013 16;25 

02/01/2013 16:26 

02/01/2013 16:27 

02/01/2013 16:2B 

02/01/2013 16:29 

02/01/2013 16:30 

02/01/2013 16;31 

02/01/2013 16:32 

02/01/2013 16:33 

02/01/2013 16:34 

02/01/2013 16:35 

02/01/2013 16:36 

02/01/2013 16:37 

02/01/2013 16:38 

02/01/2013 16:39 

02/01/2013 16:40 

02/01/2013 16:41 

02/01/2013 16:42 

02/01/2013 16:43 

Date/Time Printed: 

G12 - C2 G12 -C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.3 

2.1 

2.1 

2.1 

2.2 

2.2 

2.3 

2.2 

2.1 

2.2 

2.1 

2.2 

2.2 

2.2 

2.2 

2.2 

2.0 

2.1 

2.1 

2.0 

2.1 

2.1 

2.1 

2.1 

2.1 

2.0 

2.1 

2.2 

2.1 

2.2 

2.2 

2.1 

2.0 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

Stk 02 

• 

0-25 

14.32 

14.34 

14.34 

14 .34 

14.30 

14.32 

14 .33 

14.32 

14.32 

14.31 

14.31 

14.29 

14.29 

14.30 

14 .28 

14 .29 

14.31 

14.30 

14.31 

14.32 

14.31 

14.32 

14.30 

14.30 

14.32 

14.32 

14.30 

14 .29 

14.31 

14.31 

14 . 30 

14.32 

14 .33 

14.33 

14.32 

14 .33 

14.31 

14.32 

14.31 

14.30 

02/02/2013 12,40 

NOx Mass 

Ib/hr 

0 - 100 

4.51 

3.93 

3.93 

3.93 

3.94 

3.94 

4.51 

3.96 

3.96 

3.96 

3.97 

3.98 

3.99 

3.98 

3.99 

3.98 

3.99 

4.00 

3.99 

3.9B 

3.99 

3.98 

3.98 

3.99 

3.97 

3.96 

3.98 

3.99 

3.98 

3.99 

3.99 

3.97 

3.96 

3.95 

3.97 

3.95 

3.9B 

3.97 

3.9B 

3.98 

StkFlow 

kscfh 

0-300000 

15587 

15586 

15586 

15586 

15529 

15566 

15621 

15650 

15655 

15635 

15678 

15648 

15718 

15682 

15671 

15660 

15739 

15747 

15741 

15737 

15748 

15735 

15694 

15703 

15704 

15657 

15684 

15691 

15704 

15727 

15731 

15674 

15674 

15647 

15693 

15625 

15696 

15704 

15708 

15698 

G12-C3 G12 - C13 G12-C10 G12 - C6 G12-C7 G12-C8 G12 -C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0-1000 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.2 

0.2 

0.2 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

CO Mass 

1b/hr 

0 - 100 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.56 

0.00 

0.00 

0.00 

0.57 

0.00 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.00 

0.00 

0.00 

0.00 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.57 

0.56 

0.57 

0.56 

0.57 

0.57 

0.57 

0.57 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0 - 300 

2.06 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

2.07 

1. 97 

1. 88 

1. 97 

1. 88 

1. 96 

1. 96 

1. 97 

1. 96 

1. 96 

1. 79 

1. 88 

1. 8B 

1. 79 

1. 88 

1. 88 

1. 88 

1. B8 

1. 88 

1. 79 

1.BB 

1. 96 

1. B8 

1. 97 

1. 97 

1. B8 

1. 80 

1.89 

1. 88 

1. B9 

1. 88 

1. B8 

1. 88 

1. 8B 

Stk COe Gas hsefh 

ppm 

0-1000 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.27 

0.18 

0.18 

0.18 

0.27 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0.18 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

hsefh 

0 -10000 

5365.8 

5349.0 

5349 . 0 

5349.0 

5362.2 

5358.6 

5369.4 

5387.4 

5389.2 

5390.4 

5405.4 

5411.4 

5435.4 

5415.0 

5427.6 

5415.6 

5426.4 

5437.2 

5427.0 

5417.4 

5429.4 

5416.8 

5419.2 

5422.2 

5406.0 

5389.8 

5415.6 

5426.4 

5414.4 

5422.2 

5431.8 

5395.B 

5387.4 

5378.4 

5402.4 

5370.6 

5411. 4 

5406.0 

5415.6 

5420.4 

NH3Inj 

Ib/hr 

0-1000 

105.5 

106.3 

106.3 

106.3 

105.3 

106.5 

106.3 

108.3 

108.7 

108.7 

108.3 

108.0 

108.7 

109.7 

108.B 

108.7 

108.5 

107.5 

107.8 

10B.3 

108.3 

108.7 

109.2 

108.7 

10B.7 

107.5 

108.3 

109.3 

108.3 

106.0 

109.2 

10B.7 

107.2 

108.0 

106.0 

107.2 

107.8 

107.8 

107.0 

107.8 

2>Summary - 1-Min RATA - Continued 

MW Lo 

0-1 

55. : 

55 .. 

55.: 

55. : 

55.: 

54. : 

55. : 

55. : 

55. 

56. ( 

55. 

55.! 

56.: 

55. : 

56. 

56 . . 

56.: 

56. 

56 

56.1 

56 . . 

56.: 

56.1 

56. ( 

56. ( 

55. 

56. : 

56.1 

56. c 

56. 

56. 

55 .. 

55.: 

S5 . . 

S5. : 

55. : 

56. ( 

55. 

56 .. 

56. ( 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descri p. 

Units 

Range 

02/01/2013 16:44 

02/01/2013 16:45 

02/01/2013 16:46 

02/01/2013 16:47 

02/01/2013 16:48 

02/01/2013 16:49 

02/01/2013 16:50 

02/01/2013 16:51 

02/01/2013 16:52 

02/01/2013 16:53 

02/01/2013 16;54 

02/01/2013 16;55 

02/01/2013 16;56 

02/01/2013 16:57 

02/01/2013 16;58 

02/01/2013 16;59 

02/01/2013 17:00 

02/01/2013 17:01 

02/01/2013 17:02 

02/01/2013 17;03 

02/01/2013 17:04 

02/01/2013 17;05 

02/01/2013 17;06 

02/01/2013 17:07 

02/01/2013 17:08 

02/01/2013 17:09 

02/01/2013 17;10 

02/01/2013 17:11 

02/01/2013 17;12 

02/01/2013 17;13 

02/01/2013 17:14 

02/01/2013 17:15 

02/01/2013 17;16 

02/01/2013 17:17 

02/01/2013 17:18 

02/01/2013 17:19 

02/01/2013 17:20 

02/01/2013 17:21 

02/01/2013 17:22 

02/01/2013 17;23 

Date/Time Printed: 

G12-C2 G12 - C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0 -150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.2 

2.1 

2.2 

2.2 

2.2 

2.1 

2.0 

2.0 

2.0 

2.1 

2.0 

2.0 

2.1 

2.1 

2.2 

2.2 

2.1 

2.1 

2.2 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

2.1 

2.2 

2.1 

2.0 

2.2 

2.2 

2.1 

2.2 

2.1 

2.0 

2.1 

2.0 

2.0 

2.0 

2.0 

Stk 02 

% 

0-25 

14.31 

14.31 

14.30 

14.29 

14.30 

14.32 

14 .32 

14.34 

14.33 

14.32 

14.33 

14.32 

14.34 

14 .34 

14 .32 

14.33 

14 .34 

14 .33 

14.33 

14.31 

14 .32 

14.32 

14 . 31 

14.32 

14.32 

14.33 

14.30 

14.31 

14.32 

14.30 

14.31 

14.31 

14 .31 

14.30 

14.30 

14.30 

14.32 

14.31 

1 4. 31 

14.30 

02/02/2013 12,40 

NOx Mass 

lb/hr 

0-100 

3.99 

3.99 

4.00 

4.01 

4.00 

3.98 

3.97 

3.95 

3.95 

3.95 

3.94 

3.94 

3.92 

3.93 

3.94 

3.93 

3.94 

3.95 

3.95 

3.97 

3.97 

3.96 

3.95 

3.95 

3.96 

3.96 

3.96 

3.96 

3.95 

3.97 

3.96 

3.9S 

3.99 

4.00 

4.00 

4.00 

3.9S 

4.00 

4 .00 

4.01 

StkFlow 

ksefh 

0-300000 

15746 

15730 

1574B 

15761 

15774 

15747 

15700 

15661 

15633 

15610 

15592 

15564 

15535 

15572 

15585 

15560 

15628 

15616 

15633 

15668 

15695 

15636 

15605 

15617 

15639 

156B1 

15614 

15609 

15618 

15654 

15642 

15689 

15730 

15760 

157BO 

15769 

15735 

15776 

15776 

15806 

G12-C3 G12-CD G12-C10 G12 -C6 G12 -C7 G12-C8 G12 - C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0 -10 00 

0.3 

0.3 

0.3 

0.3 

0.2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

o 3 

0.2 

0.2 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

0.3 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

CO Mass 

lb/hr 

0-100 

0.57 

0.57 

0.57 

0.57 

0.00 

0.00 

0.00 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.56 

0.00 

0.00 

0.57 

0.00 

0.56 

0.57 

0.57 

0.57 

0.57 

0.56 

0.57 

0.57 

0.00 

0.57 

0.00 

0.00 

0.57 

0.57 

0.57 

0.57 

0.57 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0 -30 0 

1. 97 

1. 8S 

1. 97 

1. 96 

1. 97 

1. S8 

1. 79 

1. SO 

1. 80 

1. B8 

1. BO 

1. 79 

1. B9 

1. 89 

1. 97 

1. 9S 

1. 89 

1. 89 

1. 9B 

1. BB 

1. 88 

1. 88 

1. 88 

1. BS 

1. B8 

1. 89 

1. 97 

1. 88 

1. 79 

1. 97 

1. 97 

1. S8 

1. 97 

1. 88 

1. 79 

1. 88 

1. 79 

1. 79 

1. 79 

1. 79 

Stk COe Gas hsefh 

hsefh 

0 - 10000 

ppm 

0-1000 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0.27 

O.lS 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.27 

0.18 

0.18 

0.27 

0.27 

0.27 

0.27 

0 . 27 

5428.8 

5423.4 

5437.8 

5450.4 

5446.8 

5421.0 

5404.8 

5374.8 

5373.6 

5373.6 

5359.2 

5358.0 

5331.6 

5344.2 

5365.2 

5348.4 

5363.4 

5367.6 

5373.6 

5401.8 

5403.0 

5382.6 

5380.2 

5376.0 

5383.8 

5389.8 

5391.6 

5381 .4 

5376.6 

5405 .4 

5392.8 

5409.0 

5423.4 

5442.0 

5448.6 

5445.0 

5416.8 

5439.0 

5439 .0 

5457.6 

NH3Inj 

lb/hr 

0-1000 

106.7 

107.5 

107.3 

107.0 

108.8 

109.7 

108.2 

106.S 

105.5 

107.2 

107.5 

107.2 

105.0 

104.8 

105.3 

104.8 

103.S 

105.0 

105.2 

106.2 

106.8 

106.8 

106.8 

105.7 

106.5 

105.2 

106.5 

106.2 

105.7 

105.7 

105 .8 

105.2 

105.3 

108.0 

107.2 

107.3 

108.3 

108.2 

108.5 

108.5 

2>Summary - I-Min RATA - continued 

MW Lo 

0-1 

56. : 

56.: 

56 . . 

56.: 

56.: 

56.4 

56.1 

55.: 

55 .. 

55.: 

55 . . 

55.: 

54. : 

55.4 

55.: 

55.1 

55 ' 

55.: 

55. 

56.4 

56.1 

55 . 

55. 

55 . . 

55. 

55. : 

55. 

55 . ~ 

55 .. 

55. 

55. : 

55. : 

56. : 

56. : 

56.: 

56.: 

56 .1 

5 6 .. 

56 . . 

56. 

Pagf 
Group#-Channel# 

Long Desc r i p _ 

Short Descr i p . 

Units 

Range 

02/01/2013 17:24 

02/01/2013 17:25 

02/01/2013 17:26 

02/01/2013 17:27 

02/01/2013 17:28 

02/01/2013 17:29 

02/01/2013 17:30 

02/01/2013 17:31 

02/01/2013 17:32 

02/01/2013 17:33 

02/01/2013 17:34 

02/01/2013 17:35 

02/01/2013 17:36 

02/01/2013 17:37 

02/01/2013 17:38 

02/01/2013 17:39 

02/01/2013 17:40 

02/01/2013 17:41 

02/01/2013 17:42 

02/01/2013 17:43 

02/01/2013 17:44 

02/01/2013 17:45 

02/01/2013 17:46 

02/01/2013 17:47 

02/01/2013 17:48 

02/01/2013 17:49 

02/01/2013 17: 50 

02/01/2013 17:51 

02/01/2013 17:52 

02/01/2013 17:53 

02/01/2013 17:54 

02/01/2013 17:55 

02/01/2013 17:56 

02/01/2013 17:57 

02/01/2013 17:58 

02/01/2013 17:59 

02/01/2013 18:00 

02/01/2013 18:01 

02/01/2013 18:02 

02/01/2013 18:03 

Date/Time Printed: 

G12-C2 G12-C4 G12 -Cll 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.0 

2.0 

1.9 

2.0 

2.0 

2.0 

2.0 

2.0 

2.0 

2.1 

2.0 

2.0 

2.2 

2.2 

2.1 

2.1 

2.2 

2.1 

2.1 

2.0 

2.2 

2.1 

2.2 

2.2 

2.2 

2.2 

2 .2 

2.1 

2.3 

2.3 

2.0 

2.0 

2.2 

2.1 

2.0 

2.1 

2.0 

2.1 

2.1 

2.2 

Stk 02 

% 

0-25 

14 . 30 

14.31 

14.31 

14.30 

14.31 

14.33 

14.32 

14 . 32 

14.33 

14.31 

14 .31 

14.31 

14.30 

14.30 

14.31 

14.32 

14.32 

14.33 

14.33 

14.35 

14.32 

14.32 

14.32 

14.32 

14.31 

14.31 

14.31 

14.33 

14.33 

14.34 

14.37 

14.36 

14.33 

14.34 

14.37 

14 .37 

14.38 

14.37 

14 .37 

14.36 

02/02/2013 12,40 

NOx Mass 

lb/hr 

0-100 

3.99 

3.99 

3.42 

3.99 

3.99 

3.97 

3.98 

3.98 

3.97 

3.99 

3.98 

4.00 

3.99 

3.99 

3.97 

3.97 

3.96 

3.96 

3.95 

3.95 

3.97 

3.97 

3.97 

3.97 

3.97 

3.98 

3.96 

3.93 

4.50 

4.51 

3.92 

3.92 

3.94 

3.93 

3.90 

3.90 

3.89 

3.88 

3.89 

3.89 

G12 - C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

15707 

15762 

15744 

15724 

15727 

15701 

15711 

15730 

15710 

15729 

15701 

15777 

15712 

15712 

15659 

15676 

15653 

15667 

15623 

15664 

15681 

15679 

15672 

15699 

15669 

15696 

15642 

15553 

15574 

15629 

15604 

15586 

15592 

15600 

15545 

15541 

15521 

15457 

15483 

15481 

G12 -C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.3 

0.3 

0.3 

0.2 

0.2 

0.2 

0.2 

0.2 

0.3 

0.2 

0.3 

o 3 

0.3 

0.3 

0.2 

0.3 

0.3 

0.2 

0.2 

0.3 

0.2 

0.2 

0.2 

0.2 

0.2 

0.2 

0.2 

0.3 

0.2 

0.2 

0.2 

0.2 

0.2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

G12-C13 G12-C10 G12 -C6 

2>CO Mass 2>NOx Rate 2>Stk NOXe 

CO Mass 

lb/hr 

0-100 

0.57 

0.57 

0.57 

0.00 

0.00 

0.00 

0.00 

0.00 

0.57 

0.00 

0.57 

0.57 

0.57 

0.57 

0.00 

0.57 

0.57 

0.00 

0.00 

0.56 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.56 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.56 

0.56 

0.55 

0.56 

0.56 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.007 

0.006 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

Stk NOXe 

ppm 

0 -300 

1. 79 

1. 79 

1. 70 

1. 79 

1. 79 

1. 80 

1. 79 

1. 79 

1. 80 

1. 88 

1. 79 

1. 79 

1. 97 

1. 97 

1. 88 

1. 88 

1. 97 

1. 89 

1. 89 

1.80 

1. 97 

1. 88 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 89 

2.07 

2.07 

1. 81 

1. 80 

1. 98 

1. 89 

1. 81 

1. 90 

1. 81 

1. 90 

1. 90 

1. 98 

G12-C7 G12-C8 

2>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hsefh 

0-1000 0-10000 

0.27 

0.27 

0.27 

0.18 

0.18 

0.18 

0.18 

0.18 

0.27 

0.18 

0.27 

0.27 

0.27 

0.27 

0 . 18 

0.27 

0.27 

0 . 18 

0.18 

0.27 

0.18 

0.18 

0.18 

0.18 

0.18 

0.18 

0.18 

0.27 

0.18 

0.18 

0.18 

0 . 18 

0.18 

0.18 

0.18 

0.27 

0.27 

0.27 

0.27 

0.27 

5423.4 

5434.2 

5428.2 

5429.4 

5422.2 

5397.0 

5408.4 

5415.0 

5400.0 

5422.8 

5413.2 

5439.6 

5425.2 

5425.2 

5398.8 

5396.4 

5388.6 

5385.0 

5370.0 

5367.6 

5398.2 

5397.6 

5395.2 

5404.2 

5402.4 

5411.4 

5392.8 

5346.0 

5353.2 

5364.0 

5331.0 

5332.8 

5359.2 

5353.8 

5310.6 

5309.4 

5294.4 

5280.6 

5289.6 

5296 .8 

G12 -C18 

2>NH3 Inj 

NH3Inj 

lb/hr 

0-1000 

108.2 

107.3 

108.0 

108.2 

107.0 

107.3 

107.2 

107.2 

107.3 

107.5 

108.0 

107.3 

106.3 

106.3 

105.8 

105.8 

105.0 

105.3 

105.8 

106.2 

104.7 

106.0 

105.7 

105.5 

105.7 

106 . 2 

106.2 

104.5 

102.5 

104.7 

104.7 

105.0 

104.2 

104.7 

103.7 

102.7 

102.8 

102.3 

101.7 

101.7 

2>Summary - l-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

56 .. 

56. ! 

56 .• 

56. : 

56 . . 

55. 

55. 

56. t 

56. t 

56. : 

56 .• 

56.t 

56. 

56. ! 

55 .. 

55. i 

55. ! 

55 .. 

56.l 

55. 

56.l 

55 .. 

55. i 

56.l 

56.l 

56.l 

55. : 

55. : 

55. l 

55. : 

54. 

54. J 

55 . . 

55.l 

54. : 

54. : 

54. ! 

54. ( 

54 .. 

54. 

PagE 
Group#-Channel# 

Long Descri p. 

Short Descrip . 

units 

Range 

02/01/2013 18:04 

02/01/2013 18:05 

02/01/2013 18:06 

02/01/2013 18:07 

02/01/2013 18:08 

02/01/2013 18:09 

02/01/2013 18:10 

02/01/2013 18:11 

02/01/2013 18:12 

02/01/2013 18:13 

02/01/2013 18:14 

02/01/2013 18:15 

02/01/2013 18:16 

02/01/2013 18:17 

02/01/2013 18:18 

02/01/2013 18:19 

02/01/2013 18:20 

02/01/2013 18:21 

02/01/2013 18:22 

02/01/2013 18:23 

02/01/2013 18;24 

02/01/2013 18:25 

Period Average 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12-C2 G12-C4 G12-C11 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.2 

2.2 

2.2 

2.2 

2.2 

2.2 

2 . 1 

2.0 

2.0 

2.0 

2.1 

2.3 

2.3 

2.1 

2.2 

2.1 

2.1 

2.1 

2.0 

2.0 

2.0 

2.1 

2.1 

2.3 

1.8 

5.2610E+2 

100.0 

Stk 02 

• 

0-25 

14 .35 

14.35 

14.35 

14.36 

14.36 

14.37 

14.37 

14.38 

14.38 

14.38 

14.36 

14.33 

14.35 

14.36 

14.34 

14.36 

14.36 

14 . 36 

14.38 

14.38 

14.37 

14.36 

14.33 

14.38 

14.28 

3.6108E+3 

100.0 

02/02/2013 12:40 

NOx Mass 

Ib/hr 

0-100 

3.89 

3.89 

3.90 

3.90 

3.91 

3.89 

3.90 

3.89 

3.90 

3.90 

3.90 

4.47 

4.48 

3.91 

3.93 

3.93 

3.93 

3.93 

3.92 

3.92 

3.92 

3.93 

3.92 

4.52 

3.35 

9.8898E+2 

100.0 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

15464 

15440 

15468 

15500 

15532 

15506 

15517 

15533 

15544 

15546 

15519 

15485 

15559 

15558 

15587 

15623 

15616 

15614 

15634 

15637 

15615 

15617 

15627 

15806 

15440 

3.9380E+6 

100.0 

G12-C3 

2>Stk CO 

Stk co 

ppm 

0-1000 

0.3 

0.3 

0.2 

0.3 

0.3 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0. 2 

0.2 

0.2 

0.3 

0.3 

0.3 

0.3 

0.3 

0.3 

0.2 

6.9500E+l 

100.0 

G12 - C13 G12-C10 G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXe 

CO Mass 

Ib/hr 

0-100 

0.56 

0.56 

0.00 

0.56 

0.56 

0.00 

0.56 

0.56 

0.56 

0.56 

0.5 6 

0.56 

0.56 

0.56 

0.56 

0.00 

0.00 

0.00 

0.56 

0.56 

0.56 

0.56 

0.43 

0.57 

0.00 

1.0761E+2 

100.0 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.006 

1.7529E+0 

100.0 

Stk NOXe 

ppm 

0-300 

l. 98 

1. 98 

l. 98 

1. 98 

l. 98 

l. 99 

1. 90 

1. 81 

1. 81 

l.81 

1. 89 

2.07 

2.07 

l. 89 

1. 98 

1. 89 

l. 89 

1. 89 

1. 81 

1. 81 

1. 81 

1. 89 

l. 87 

2.07 

1. 62 

4.7233E+2 

100.0 

G12-C7 G12-C8 G12-C18 

2>Stk COe 2>Gas Flow 2>NH3 Inj 

Stk COe Gas hsefh NH3Inj 

ppm hsefh Ib/hr 

0-1000 

0.27 

0.27 

0.18 

0.27 

0.27 

0 .18 

0.27 

0.27 

0.27 

0 .27 

0.27 

0.27 

0.27 

0.27 

0.27 

0.18 

0.18 

0 . 18 

0.27 

0.27 

0.27 

0.27 

0.25 

0.27 

0.18 

6.2550E+1 

100.0 

0-10000 

5299.2 

5290.8 

5300. 4 

5303.4 

5314.2 

5297.4 

5301.0 

5298 .6 

5302.2 

5302.8 

5310.0 

5322.6 

5331.6 

5323.2 

5349.6 

5345.4 

53 43.0 

5342.4 

5332.8 

5334.0 

5334.6 

5343.6 

5372.5 

5457.6 

52BO.6 

1.3538E+6 

100.0 

0 -1000 

101. 8 

10l. 2 

102.3 

101. 8 

103.0 

101.8 

102.5 

101.7 

103.5 

102.0 

101.8 

102.2 

102.7 

102.7 

102.7 

103.0 

103.0 

103.2 

103.7 

104.0 

103.0 

102.0 

106.4 

109.7 

101.2 

2.6B08E+4 

100.0 

2>Summary - 1-Min RATA - cont inued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

54.: 

53.1 

54 

54.: 

54.: 

54.! 

54.: 

54.( 

54.' 

54.: 

54. 

54.1 

54.: 

54.' 

54 

55.' 

55.' 

54.1 

54.: 

55.: 

54.: 

54.' 

55.3 

56. 

53. 

1.3941E+ 

100. 

PagE 
Data Summary Report 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

~~I\.l\ Ok:+ 2-

Desert Hot Springs , CA 92240 

Source: 

7-2 I~TIl.- PM - =t~-I Data Group: 

Report Name : 

Start of Report : 

Turbine 2 

2 >1 - Min Cales 

2 >Summary - I-Min RATA 

02/01/2013 08,11 

G12 - C4 

End of Report, 02/01/2013 12,22 

GI2-CII G12 -C13 

fM TRACE 

Environmental System"" ITIC. 

validation: All Available Data 

Group#-Channel# GI2-ClO G12-C6 G12 - C7 G12-Ca G12-C 

Long Descrip. 

Short Descrip. 

units 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 

Stk CDc Gas hscfh 

G12-C18 

2>NlD Inj 

NH3Inj 

Ib/hr 

0-1000 

2>MW Lo 

Range 

02/01/2013 08:11 

02/01/2013 08:12 

02/01/2013 08:13 

02/01/2013 08:14 

02/01/2013 08:15 

02/01/2013 08:16 

02/01/2013 08:17 

02/01/2013 08 : 18 

02/01/2013 08:19 

02/01/2013 08:20 

02/01/2013 08:21 

02/01/2013 08:22 

02/01/2013 08:23 

02/01/2013 08:24 

02/01/2013 08:25 

02/01/2013 08:26 

02/01/2013 08:27 

02 /01/2013 08:28 

02/01/2013 08:29 

02/01/ 2 013 08:30 

02/01/2013 08:31 

02/01/2013 08:32 

02/01/2013 08;33 

02/01/2013 08:34 

02/01/2013 08:35 

02/01/2013 08:36 

02 /01/2013 08 : 37 

02/01/2013 08:38 

02 /01/ 2 013 08:39 

02/01/2013 08:40 

Date/Time Printed: 

1.3 

1. 4 

1.5 < 

0.5 C 

0.0 C 

0.0 C 

99.0 C 

133.6 C 

133.7 C 

39 . 4 C 

4.6 C 

4.6 C 

3 . 4 C 

2.3 < 

3.0 

2.7 

3.1 

2 . 7 

3 . 0 

2.6 

3 . 1 

2.9 

2.B 

2 . 9 

2.9 

2.9 

2.9 

2 . 8 

2.B 

2.9 

Stk 02 

• 

0-25 

13 .39 

13 .39 

13 . 41< 

20 . 64 C 

22.45 C 

22.46 C 

3 . 92 C 

0 . 07 C 

0.06 C 

0.05 C 

0.04 C 

0.04 C 

10.96 C 

13 .43 < 

13 .39 

13 . 42 

13.3 9 

13 . 44 

13.39 

13. 43 

13.39 

13 .3 9 

13 .39 

13.39 

13 .38 

13 .38 

13.38 

13 . 39 

13.39 

13.39 

02/01/2013 16,10 

NOx Mass 

Ib/hr 

0-100 

2.91 

2 .90 

2.91 

2.90 C 

0.00 C 

0.00 C 

89 . 61C 

100 . 00C 

100.00C 

29.80 C 

3.64 C 

3.63 C 

5 . 08 C 

5.08 

6.53 

5 . 79 

6.52 

5.79 

6.52 

5.79 

6.5 2 

5.8 1 

5.81 

5 . 80 

5.81 

5.80 

5.81 

5.78 

5.78 

5.79 

17626 

17584 

17662 

300000 C 

DC 

DC 

7810 C 

6360 C 

6354 C 

6346 C 

6350 C 

6332 C 

13298 C 

17676 

17575 

17620 

17552 

17659 

17555 

17625 

17552 

17604 

17612 

17558 

17584 

17552 

17569 

175 2 5 

17511 

17552 

1.6 

2 . 6 

1. 3 < 

2.1 C 

0.0 C 

0.0 C 

412.2C 

891.4C 

893.5 C 

475.8C 

9 . 7 C 

9.1 C 

5.8 C 

2 . 5< 

1.9 

1.4 

1.4 

1.4 

1.2 

1.3 

1.0 

O.B 

0.9 

0 . 9 

O.B 

0.8 

0.8 

O.B 

O.B 

O. B 

CO Mass 

Ib/hr 

0-100 

2.18 

3.63 

1. 45 

6 . 53 C 

0.00 C 

0.00 C 

100.00C 

100.00C 

100.00C 

100.00C 

4 . 37 C 

4.35 C 

5.81 C 

2 . 90 

2.18 

1.45 

1.45 

1 .4 5 

1 .4 5 

1. 45 

1. 45 

0.73 

1. 45 

1.45 

0.73 

0.73 

0.73 

0 . 72 

0 . 72 

0.72 

NOx Rate 

Ib/mmBtu 

0-1 

0.004 

0 . 004 

0.004 

0.004 C 

0.000 C 

0 . 000 C 

0.123 C 

0.139C 

0.139 C 

0.041 C 

0 . 005 C 

0 . 005 C 

0.007 C 

0.007 

0.009 

0.008 

0.009 

0 . 008 

0.009 

0.008 

0.009 

0.008 

0 . 008 

0 . 008 

0 . 008 

0.008 

0 . 008 

0.008 

0 . 008 

0.008 

Stk NOXc 

ppm 

0- 300 

1. 02 

1.10 

1.18 < 

11.35C 

0.00 C 

0.00 C 

34 . 40C 

37.84 C 

37.85 C 

11.15 C 

1 . 30 C 

1 . 30 C 

2.02 C 

1.82 < 

2.36 

2.13 

2 .44 

2.14 

2.36 

2 .05 

2.44 

2 .28 

2 . 20 

2.28 

2 . 28 

2. 2 8 

2 . 28 

2.20 

2.20 

2.28 

ppm hscfh 

0-1000 0-10000 

1.26 

2.04 

1.02 < 

47.65 C 

0.00 C 

0 . 00 C 

143.23C 

252.48 C 

252 . 96C 

134.64 C 

2 . 74 C 

2.57 C 

3.44 C 

1.97 < 

1.49 

1.10 

1.10 

1.11 

0.94 

1. 03 

0.79 

0 . 63 

0 . 71 

0.71 

0.63 

0.63 

0 . 63 

0.63 

0 .6 3 

0.63 

6 925.2 

6909 . 0 

6921.0 

6907.2 

6913.2 

6918.6 

6938 . 4 

6931.2 

6928.2 

6922.2 

6930.0 

6910.2 

6915.6 

6907.8 

6905. 4 

6895.2 

6896. 4 

6892.2 

6897.6 

6888.0 

6896.4 

6916.8 

6919.8 

6898.8 

6918 . 0 

6905.4 

6912.0 

6885.6 

6880 . 2 

6896. 4 

110 . 0 

110.0 

110 . 0 

110.0 

110 . 0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110 . 0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

MW Lo 

0-1 

79.: 

79.: 

79. ' 

79. : 

79. ! 

79. : 

79. ! 

79. ! 

79 .. 

79 . . 

80.1 

79.! 

79. ! 

79. ' 

79. ' 

79.: 

79. ! 

79.: 

79. ! 

79. ! 

79. ' 

80.1 

80. : 

80 . : 

80.1 

80.1 

79 .. 

79 . 

79 .. 

80 . ; 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descrip. 

units 

Range 

02/01/2013 08:41 

02/01/2013 08:42 

02/01/2013 08:43 

02/01/2013 08:44 

02/01/2013 08:45 

02/01/2013 08;46 

02/01/2013 08:47 

02/01/2013 08;48 

02/01/ 20 13 08:49 

02/01/2013 OS:50 

02/01/2013 08:51 

02/01/2013 08:52 

02/01/2013 08:53 

02/01/2013 08;54 

02/01/2013 08:55 

02/01/2013 08;56 

02/01/2013 08:57 

02/01/2013 08:58 

02/01/2013 08:59 

02/01/2013 09;00 

02/01/2013 09:01 

02/01/2013 09:02 

02/01/2013 09:03 

02 /01/2013 09;04 

02/01/2013 09:05 

02/01/2013 09:06 

02/01/2013 09:07 

02/01/2013 09;08 

02/01/2013 09;09 

02/01 /2013 09:10 

02/01/2013 09:11 

02/01/2013 09:12 

02/01/2013 09:13 

02/01/2013 09:14 

02/01/2013 09;15 

02/01/2013 09:16 

02/01/2013 09:17 

02/01/2013 09:18 

02/01/2013 09:19 

02/01/2013 09:20 

Date/Time Printed: 

G12-C2 G12-C4 GI2 - CII 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.8 

2.7 

2.8 

2.8 

2.7 

2.8 

2.7 

2.8 

2.7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.6 

2.6 

2.5 

2.7 

2.7 

2.7 

2.5 

2.5 

2.6 

2.5 

2.6 

2.6 

2.6 

2.6 

2.6 

2.5 

2.6 

2.4 

2.4 

2.4 

2.5 

2.5 

2.5 

2.5 

2.5 

Stk 02 

t 

0-25 

13 .40 

13 .41 

13 .40 

13.42 

13.42 

13. 4 1 

13.41 

13. 41 

13 .42 

13 .40 

13 .40 

13 .40 

13 .40 

13 .39 

13 .41 

13.41 

13.42 

13 .41 

13 .40 

13 .41 

13 .40 

13.39 

13 .40 

13 . 39 

13.40 

13.41 

13 .39 

13 .39 

13 .40 

13 .41 

13 .41 

13 .40 

13.41 

13 .41 

13.41 

13 .41 

13 .42 

13 .42 

13 .40 

13 .41 

02/01/2013 16,10 

NOx Mass 

Ib/hr 

0-100 

5.79 

5.80 

5.78 

5.77 

5.77 

5.78 

5.78 

5.78 

5.77 

5.79 

5.80 

5.80 

5.82 

5.83 

5.81 

5.81 

5.80 

5.08 

5.81 

5.81 

5.82 

5.11 

5.10 

5.83 

5.09 

5.81 

5.82 

5.81 

5.82 

5.81 

5.08 

5.82 

5.09 

5.09 

5.08 

5.07 

5.07 

5.07 

5.08 

5.06 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

17554 

17625 

17542 

17543 

17555 

17546 

17547 

17547 

17563 

17571 

17594 

17608 

17652 

17655 

17645 

17647 

17652 

17627 

17616 

17642 

17655 

17684 

17674 

17662 

17646 

17659 

17623 

17604 

17663 

17661 

17651 

17655 

17671 

17674 

17636 

17592 

17634 

17638 

17605 

17581 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.8 

0.8 

0.8 

0.7 

0.7 

0.8 

0.8 

0.7 

0.8 

0.8 

0.8 

0.8 

0.8 

0.7 

0.7 

0.7 

0.7 

0.8 

0.8 

o.s 

0.7 

o.s 

0.8 

0.7 

0.8 

0.8 

o.s 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.8 

0.7 

0.7 

0.8 

G12-C13 G12 - C10 G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

0.72 

0.73 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.72 

0.72 

0.72 

0.73 

0 . 72 

NOx Rate 

lb/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

o.ooa 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

o.ooa 

0.008 

0.007 

0.008 

0.008 

0.008 

0.007 

0.007 

0.008 

0.007 

0.008 

0.008 

O.OOB 

0.008 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

2.20 

2.13 

2.20 

2.21 

2.13 

2.21 

2.13 

2.21 

2.13 

2.12 

2.12 

2. OS 

2.12 

2.12 

2.05 

2.05 

2.05 

1. 97 

2.12 

2.13 

2.12 

1. 96 

1. 97 

2.04 

1. 97 

2.05 

2.04 

2.04 

2.05 

2.05 

1. 97 

2.05 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

G12-C7 G12-CS 

2>Stk COc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

0.63 

0.63 

0.63 

0.55 

0.55 

0.63 

0.63 

0.55 

0.63 

0.63 

0.63 

0.63 

0.63 

0.55 

0.55 

0.55 

0.55 

0.63 

0.63 

0.63 

0.55 

0 .6 3 

0.63 

0 . 55 

0.63 

0.63 

0.63 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.63 

0.55 

0.55 

0.63 

6888.0 

6906.6 

6883.2 

6865.2 

6870.0 

6875.4 

6876.0 

6876.0 

6873.0 

6894.6 

6903.6 

6909.0 

6926.4 

6936.6 

6914.4 

6915.0 

6907.8 

6907.2 

6912.0 

6913.2 

6927.6 

6948.0 

6934.8 

6939.6 

6924.0 

6919.8 

6924.0 

6916.8 

6930.6 

6920.4 

6916.8 

6927.6 

6924.6 

6925.8 

6910.8 

6893.4 

6900.6 

6902.4 

6907.8 

6889.2 

GI2-ClS 

2>NH3 Inj 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

GI2-C 

2>MW Lo 

MW Lo 

0-1 

79.! 

79. ' 

79. 

79. 

79.: 

79. ! 

79.: 

79.: 

79. ! 

79. : 

79 .. 

79. : 

80 . . 

80.! 

80.! 

80.1 

80 .. 

80. 

80.1 

80.: 

80. ! 

80 .. 

80. ! 

80. : 

80 . . 

80.1 

so 

80. : 

80.1 

80.! 

80 

80 .. 

80 

80 

80. : 

79 .. 

80. ( 

80. : 

80. ( 

79. ! 

PagE 
Group# - Channel# 

Long Descrip . 

Sho rt Descrip . 

units 

Range 

02/01/2013 09:21 

02/01/2013 09:22 

02/01/2013 09:23 

02/01/2013 09:24 

02/01/2013 09:25 

02/01/2013 09:26 

02/01/2013 09:27 

02/01/2013 09:28 

02/01/2013 09:29 

02/01/2013 09:30 

02/01/2013 09:31 

02/01/2013 09:32 

02/01/2013 09:33 

02/01/2013 09:34 

02/01/2013 09:35 

02/01/2013 09:36 

02/01/2013 09:37 

02/01/2013 09:38 

02/01/2013 09:39 

02/01/2013 09:40 

02/01/2013 09:41 

02/01/2013 09:42 

02/01/2013 09:43 

02/01/2013 09:44 

02/01/2013 09:45 

02/01/2013 09:46 

02/01/2013 09:47 

02/01/2013 09:48 

02/01/2013 09:49 

02/01/2013 09:50 

02/01/2 013 09:51 

02/01/2013 09:52 

02/01/2013 09:53 

02/01/2013 09:54 

02/01/2013 09:55 

02/01/2013 09:56 

02/01/2013 09:57 

02/01/2013 09:58 

0 2 /01/2013 09:59 

02/01/2013 10:00 

Date/Time Printed: 

G12-C2 G12-C4 G12-Cll G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.6 

2.5 

2.5 

2.5 

2.6 

2.5 

2.6 

2.6 

2.5 

2.4 

2.4 

2.4 

2.4 

2.4 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.4 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.5 

2.5 

2 . 6 

2.6 

2.6 

2.4 

2.5 

2.5 

2.6 

2.6 

2.4 

2.4 

Stk 02 

\ 

0-25 

13 . 40 

13. 4 0 

13.40 

13 .40 

13 .41 

13 .41 

13 . 4 0 

13 . 4 1 

13 .41 

13. 4 0 

13.42 

13 .41 

13 . 41 

13 . 4 1 

13 . 4 1 

13 .4 0 

13 .4 1 

13 .41 

13.41 

13 . 4 0 

13 .41 

13 .41 

13 . 41 

13 . 40 

13. 4 0 

13.40 

13.39 

13 . 39 

13 .40 

13 . 40 

13 .39 

13 .39 

13. 4 0 

13.42 

13 .41 

13 .40 

13.39 

13.39 

13 . 39 

13 .40 

02/01/2013 16,10 

NOx Mass 

1b/hr 

0-100 

5.80 

5.08 

5.08 

5.08 

5.79 

5.06 

5.82 

5.81 

5.06 

5.08 

5.06 

5.07 

5.06 

5.06 

5.07 

5.09 

5.09 

5.09 

5.08 

5.08 

5.06 

5.80 

5.80 

5.80 

5.81 

5.82 

5.80 

5.81 

5.08 

5.0B 

5.81 

5.B2 

5.84 

5 .09 

5.10 

5.11 

5.84 

5.85 

5.10 

5.09 

StkFlow 

kscfh 

0-300000 

17602 

17626 

17625 

17609 

17589 

17579 

17654 

17647 

17582 

1762B 

17584 

17593 

17556 

17572 

17592 

17655 

17664 

17664 

17627 

17616 

17561 

17621 

17621 

17602 

17614 

17646 

17578 

17598 

17600 

17611 

17 6 15 

17641 

17712 

17683 

17722 

17727 

17704 

17728 

1 7650 

17651 

G12-C3 GI2-C13 G12 -CI0 G12-C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

0.7 

0.7 

0.7 

0.6 

0.6 

0.6 

0.6 

0.6 

0.6 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.6 

0.6 

0.6 

0.6 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.6 

0.6 

0.6 

0.6 

0.6 

0.6 

0.6 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

0.7 

CO Mass 

1b/hr 

0-100 

0.73 

0.73 

0.73 

0.73 

0.72 

0.72 

0.73 

0.73 

0.72 

0.73 

0.72 

0.72 

0.72 

0.72 

0 . 72 

0.73 

0.73 

0.73 

0.73 

0.73 

0.72 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.007 

0.007 

0.007 

0.008 

0.007 

O.OOB 

O.OO B 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.007 

0.00 8 

0.00 8 

0.008 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

2.05 

1. 97 

1. 97 

1. 97 

2.05 

1. 97 

2.05 

2.05 

1. 97 

1. 89 

1. 89 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

l. 97 

1. 89 

2.05 

2.05 

2.05 

2.05 

2.05 

2.12 

2.04 

1. 97 

1. 97 

2.04 

2.04 

2.05 

1. 89 

1. 97 

1. 97 

2.04 

2.04 

1. 89 

1. 89 

Stk COe Gas hscfh 

ppm hsefh 

0-1000 0 - 10000 

0.55 6906.6 

0.55 6916.2 

0.55 6915.6 

0.47 6909.6 

0.47 

0.47 

0.47 

0 . 47 

0 . 47 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0. 4 7 

0.47 

0.47 

0.47 

0.55 

0.55 

0.55 

0.55 

0.55 

0 . 55 

0.55 

0.47 

0.47 

0 . 47 

0.47 

0 . 47 

0 . 47 

0.47 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

0.55 

6892.2 

6888.6 

6927.0 

6915.0 

6B89.B 

6916.8 

6881.4 

6894.0 

6879.6 

6885.6 

6893.4 

6927.6 

6921.6 

6921.6 

6907.2 

6912.0 

6881.4 

6904.8 

6904.8 

6906.6 

6911.4 

6924.0 

6906.6 

6914.4 

6906.0 

6910.2 

6921.0 

6931.2 

6949.8 

6919.8 

6944.4 

6955.8 

6955.B 

6965.4 

6934.8 

6925.8 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

2>Summary - 1-Min RATA - Continued 

MW La 

0-1 

79 . . 

79. 

80. : 

79. ! 

80. ! 

79 .. 

79. 

80. ! 

79. ! 

80.1 

79 .. 

79 

79.: 

79 .. 

79.! 

80. : 

79. : 

79. : 

79. : 

80 . 1 

79. : 

79. 

79. : 

79. : 

79. ! 

79.: 

80. 1 

79. : 

79 .. 

80. : 

80.1 

80 . . 

80 .. 

80.1 

80.: 

80.: 

80. ! 

BO. 

80. ! 

80.1 

PagE 
Group#-Channe l# 

Long Descrip . 

Short Descrip . 

Units 

Range 

02/01/2013 10:01 

02/01/2013 10:02 

02/01/2013 10:03 

02/01/2013 10:04 

02/01/2013 10:05 

02/01/2013 10:06 

02/01/2013 10:07 

0 2 /01/2013 10:08 

02/01/2013 10:09 

02/01/2013 10:10 

02/01/2013 10:11 

02/01/2013 10:12 

02/01/2013 10:13 

02/01/2013 10;14 

02/01/2013 10:15 

02/01/2013 10:16 

02/01/2013 10:17 

02/01/2013 10:lB 

02/01/2013 10:19 

02/01/2013 10:20 

02/01/2013 10;21 

02/01/2013 10:22 

02/01/2013 10:23 

0 2 /01/2013 10;24 

02/01/2013 10:25 

02/01/2013 10;26 

02/01/2013 10:27 

02/01/2013 10:28 

02/01/2013 10:29 

02/01/2013 10:30 

02/01/2013 10:31 

02/01/2013 10:32 

02/01/2013 10:33 

02/01/2013 10:34 

02/01/2013 10:35 

02/01/2013 10;36 

02/01/2013 10:37 

02/01/ 2 013 10:38 

02/01/2013 10:39 

02/01/2013 10:40 

Date/Time Printed: 

G12-C2 G12-C4 G12 - C11 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.5 

2.5 

2.5 

2.' 

2.' 

2.5 

2.5 

2.' 

2.' 

2.' 

2.' 

2.' 

2.5 

2.6 

2.' 

2.' 

2.5 

2.' 

2.' 

2.5 

2.5 

2.' 

2.' 

2.' 

2.' 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.5 

2.' 

2.5 

2.5 

Stk 02 

• 

0-25 

13 .41 

13.40 

13.41 

13 .42 

13. 4 2 

13 .4 1 

13. 4 0 

13 .4 0 

13 .4 1 

13.41 

13 .42 

13.41 

13.41 

13 .40 

13 .41 

13 .41 

13 .40 

13.41 

13.43 

13. 4 2 

13 .39 

13 . 4 1 

13.41 

13 . 42 

13 .41 

13 . 43 

13 .43 

13 .43 

13.43 

13 .42 

13.41 

13 .42 

13 .42 

13 . 42 

13 .41 

13 .41 

13 . 41 

13 .4 1 

13 .4 1 

13. 4 1 

02/01/2013 16,10 

NOx Mass 

Ib/hr 

0 - 100 

5.10 

5.09 

5.09 

5.09 

5.10 

5.11 

5.11 

5.11 

5.10 

5.10 

5.08 

5.08 

5.07 

5.BO 

5.08 

5.09 

5.10 

5.09 

5. 0,8 

5.09 

5.09 

5.07 

5.07 

5.05 

5.06 

5.04 

5.05 

5.05 

5.06 

5.06 

5.06 

5.07 

5.06 

5.07 

5.07 

5.07 

5.07 

5.05 

5 . 05 

5.07 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

17693 

17664 

17668 

17692 

17716 

17726 

17730 

17710 

17716 

17696 

17650 

17625 

17598 

17603 

17622 

17667 

17674 

17657 

17682 

17698 

17613 

17612 

17596 

17571 

17569 

17559 

17573 

17574 

17599 

17606 

17579 

17621 

17600 

17635 

17604 

17587 

17595 

17543 

17535 

17585 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.7 

0.6 

0.5 

0.6 

0.7 

0.6 

0.6 

0.7 

0.7 

0.7 

0.6 

0.6 

O.B 

0.7 

0.6 

0.7 

0.7 

0.7 

0.6 

0.7 

0.6 

0.6 

0.6 

0.6 

0.7 

0.6 

0.6 

0.6 

0.6 

0.5 

0.5 

0.6 

0.6 

0.6 

0.6 

0.6 

0.6 

0 . 7 

0.7 

0. 7 

G12-C13 G12 -C10 G12 -C6 

2>CO Mass 2>NOx Rate 2>Stk NOXe 

CO Mass 

Ib/hr 

0-100 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0 . 73 

0.73 

0 . 73 

0.73 

0.72 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.73 

0.72 

0.72 

0 . 72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

0 . 72 

0.72 

0.72 

0.72 

0.72 

0.72 

0.72 

NOx Rate 

lb/mmBtu 

0 - 1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

O.OOB 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1. 97 

1. 97 

1. 97 

1. 89 

1. 89 

1. 97 

1. 97 

1. 89 

1. 89 

1. 89 

1. 89 

1. B9 

1. 97 

2.05 

1. 89 

1. 89 

1. 97 

1. 89 

1. 90 

1. 97 

1. 96 

1. 89 

1. 89 

1. 89 

1. 89 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 89 

1. 97 

1. 97 

G12-C7 G12 - C8 

2>Stk COe 2>Gas Flow 

Stk COe Gas hscfh 

ppm hscfh 

0-1000 0-10000 

0.55 

0.47 

0.39 

0.47 

0.55 

0 . 47 

0.47 

0.55 

0 . 55 

0.55 

0.47 

0.47 

0.63 

0.55 

0.47 

0.55 

0.55 

0.55 

0.47 

0.55 

0.47 

0.47 

0.47 

0.47 

0.55 

0.47 

0.47 

0.47 

0.47 

0.39 

0.39 

0.47 

0.47 

0.47 

0.47 

0.47 

0.47 

0.55 

0.55 

0.55 

6933.0 

6931.2 

6923 . 4 

6923 . 4 

6933.0 

6946.2 

6957.0 

6949.2 

6942.0 

6934.2 

6907.2 

6906.6 

6895.8 

6907.2 

6905.4 

6922.8 

6934.8 

6919.2 

6910.2 

6925.8 

6920.4 

6901.2 

6895.2 

6876.0 

6884.4 

6862.2 

6867.6 

6868.2 

6877.8 

6889.8 

6888.6 

6895.8 

6887.4 

6901.2 

6898.2 

6891.6 

6894 . 6 

6874.2 

6871.2 

6891.0 

G12 -C18 

2 >NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

l10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - 1-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

BO. 

79. 

BO . r 

BO 

80.: 

80 .: 

80. ! 

80. : 

80.: 

80 .. 

80.1 

80.1 

79 . . 

80. : 

79.1 

79.1 

79. : 

79.1 

79 .. 

79 .. 

80 .1 

79 .. 

79 .. 

78 . 

79. ! 

79.: 

78. : 

79.: 

79. : 

79 . ~ 

79 .. 

79. ! 

79 .. 

79. 

79. 

79. 

79. 

79. : 

79 . 1 

79.: 

Pag{ 
Group#-Channe l# 

Long Descrip . 

Short Descrip. 

Units 

Range 

02/01/2013 10:41 

02/01/2013 10:42 

02/01/2013 10:43 

02/01/2013 10:44 

02/01/2013 10:45 

02/01/2013 10:46 

02/01/2013 10:47 

02/01/2013 10:48 

02/01/2013 10:49 

02/01/2013 10:50 

02/01/2013 10:51 

02/01/2013 10:52 

02/01/2013 10:53 

02/01/2013 10:54 

02/01/2013 10:55 

02/01/2013 10:56 

02/01 /2013 10:57 

02/01/2013 10:58 

02/01/2013 10:59 

02/01/2013 11:00 

02/01 /2013 11:01 

02/01/2013 11:02 

02/01/2013 11:03 

02/01/2013 11:04 

02/01/2013 11:05 

02/01/2013 11:06 

02/01/2013 11:07 

02/01/2013 11:08 

02/01/2013 11;09 

02/01/2013 11:10 

02/01/2013 11:11 

02/01/2013 11:12 

02/01/2013 11:13 

02/01/2013 11:14 

02/01/2013 11:15 

02/01/2013 11:16 

02/01/2013 11:17 

02/01/2013 11:18 

02/01/2013 11:19 

02/01/2013 11:20 

Date/Time Printed: 

G12 -C2 G12-C4 G12-Cll 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 

2.5 

2.5 

2.5 

2.5 

2.5 

2.4 

2.5 

2.4 

2.6 

2.5 

2.5 

2.4 

2.5 

2.5 

2.4 

2.5 

2.4 

2.5 

2.5 

2.4 

2.5 

2.4 

2 .4 

2.4 

2.4 

2.5 

2.5 

2. 4 

2.4 

2.5 

2.5 

2.4 

2.6 

2.5 

2.5 

2.3 

2.4 

2.5 

2.5 

2.5 

Stk 02 

% 

0-25 

13 .41 

13 .42 

13 .42 

13 .42 

13 .42 

13 .41 

13 .41 

13.39 

13.39 

13. 39 

13.39 

13 .41 

13 .40 

13 .40 

13.39 

13.39 

13.39 

13.39 

13 . 39 

13.39 

13 .38 

13 .38 

13.38 

13.40 

13.41 

13.40 

13. 4 0 

13 .42 

13 .40 

13 .40 

13 .40 

13.41 

13.39 

13 .4 0 

13 .39 

13 .39 

13 .41 

13 .40 

13. 4 0 

13.40 

02/01/2013 16,10 

NOx Mass 

Ib/hr 

0-100 

5.06 

5.05 

5.06 

5.05 

5.07 

5.08 

5 . 10 

5.11 

5.86 

5.14 

5.14 

5.12 

5.13 

5.14 

5.15 

5.16 

5.16 

5.15 

5.16 

5.15 

5.15 

5.15 

5.14 

5.12 

5.13 

5.14 

5.12 

5.10 

5.13 

5.13 

5.13 

5.12 

5.85 

5.13 

5.16 

5.15 

5.12 

5.11 

5.11 

5.10 

G12 - C20 

2>StkFlow 

StkFlow 

ksefh 

0-300000 

17572 

17548 

17577 

17571 

17634 

17645 

17720 

17708 

17742 

17806 

17809 

17792 

17790 

17836 

17823 

17867 

17878 

17839 

17855 

17847 

17797 

17805 

17779 

17749 

17797 

17827 

17758 

17738 

17778 

17788 

17772 

17774 

17734 

17799 

17870 

17835 

17769 

17716 

17721 

17695 

G12 -C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

0.9 

1.0 

1.1 

1.1 

1.2 

1.5 

2 '. 4 

2. 5 

2.6 

2.5 

2.5 

2 . 7 

2.B 

2 . 5 

2.4 

2.4 

2.4 

2.1 

1.9 

1.9 

1.6 

1.5 

1.5 

1.6 

1.B 

1.6 

1.3 

1.1 

1.6 

1.4 

1.7 

1.5 

1.5 

1.4 

1.6 

1.7 

1.6 

1.5 

1.5 

1.8 

G12-C13 G12-CI0 G12 - C6 

2>CO Mass 2>NOx Rate 2>Stk NOXe 

CO Mass 

lb/hr 

0-100 

1. 45 

1.44 

1.44 

1.44 

1.45 

2.18 

2.92 

2.92 

3.66 

2.94 

2.94 

3.66 

3 . 66 

2.94 

2.94 

2.95 

2.95 

2.94 

2.21 

2.21 

2.21 

2.21 

2.20 

2.19 

2.20 

2.20 

1.46 

1. 46 

2.20 

1.47 

2.20 

2.19 

2.19 

1. 47 

2.21 

2.21 

2.19 

2.19 

2.19 

2.19 

NOx Rate 

lb/mmBtu 

0 - 1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1. 97 

1. 97 

1. 97 

1. 97 

1. 97 

1. 89 

1. 97 

1. 89 

2.04 

1. 96 

1. 96 

1. B9 

1. 97 

1. 97 

1. 89 

1. 96 

1. 89 

1. 96 

1. 96 

1. B9 

1. 96 

1. B8 

1. 88 

1. 89 

1. 89 

1. 97 

1. 97 

1. 89 

1.89 

1. 97 

1. 97 

1. 89 

2.04 

1. 97 

1. 96 

1. 81 

1. 89 

1. 97 

1 . 97 

1. 97 

G12-C7 G12-C8 

2>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hsefh 

0-1000 0-10000 

0.71 

0.79 

0.87 

0.87 

0.95 

1.18 

1. 89 

1. 96 

2.04 

1. 96 

1. 96 

2.13 

2.20 

1. 97 

1. 89 

1. 89 

1. 89 

1. 65 

1. 4 9 

1. 49 

1.26 

1.18 

1.18 

1. 26 

1.42 

1. 26 

1. 02 

0.87 

1. 26 

1.10 

1. 34 

1.18 

1.18 

1.10 

1. 26 

1. 34 

1. 26 

1.18 

1.18 

1. 42 

6885.6 

6867.0 

6878.4 

6876.0 

6900.6 

6914.4 

6943 . 8 

6957.6 

6970.8 

6996.0 

6997.2 

6972.0 

6980.4 

6998.4 

7002.6 

7020.0 

7024.2 

7009.2 

7015.2 

7012.2 

7002.0 

7005.0 

6994.8 

6964.2 

6973.8 

6994.8 

6967.8 

6941. 4 

6975.6 

6979.8 

6973.2 

6964.8 

6967.8 

6984.0 

7021.2 

7007.4 

6963.0 

6951.6 

6953.4 

6943 . 2 

G12 - C18 

2>NH3 Inj 

NH3Inj 

Ib/hr 

0 - 1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

79. : 

79 

79 . . 

79.: 

79.: 

79 .. 

79 . . 

7 9 .. 

80.1 

80 .. 

BO. 

BO .1 

80.1 

80. : 

80 .. 

80.: 

81.1 

81.1 

80 .. 

BO. 

80 .. 

81.1 

80. ! 

80.1 

80 .1 

80 . . 

80. ! 

80.1 

80 . 1 

BO. 

BO .. 

BO .1 

80.: 

81.: 

80. : 

80 .. 

80.1 

79 . 

80.1 

79 .. 

Pagf 
Group# - Channel# 

Long Descr ip . 

Short Descrip. 

Units 

Range 

0 2 /01/2013 11:21 

02/01/2013 11:22 

0 2 /01/2013 11:23 

02/01/2013 11:24 

02/01/2013 11:25 

02/01/2013 11:26 

02/01/2013 11:27 

0 2 /01/2013 11:28 

02/01/2013 11:29 

0 2 /01/2013 11:30 

0 2 /01/ 2 013 11:31 

02/01/2013 11:32 

02/01/2013 11:33 

02/01/2013 11:34 

02/01/2013 11:35 

0 2 /01/2013 11 : 36 

02/01/2013 11 : 37 

02/01/2013 11:38 

02/01/2013 11:39 

02/01/2013 11: 4 0 

02/01/2013 11:41 

02/01/ 2 013 11:42 

02/01/2013 11:43 

02/01/2013 11:44 

02/01/2013 11 : 45 

02/01/2013 11:46 

02/01/2013 11:47 

02/01/2013 11: 4 8 

0 2 /01/ 2 013 11 :4 9 

02/01/2013 11:50 

0 2 /01/2013 11 : 51 

02/01/2013 11:52 

02/01/2013 11:53 

02/01/2013 11:54 

02/01/2013 11:55 

02/01/ 2 013 11:56 

02/01/2013 11:57 

02/01/ 2 013 11:58 

02/01/2013 11:59 

02/01 / 2 013 12 : 00 

Date/Time Printed: 

G1 2 -C2 G12-C4 G12 -Cll G12 - C20 

2 >Stk NOx 

Stk NOx 

2>Stk 02 2>NOx Mass 2>StkFIow 

ppm 

0 - 150 

2.5 

2.4 

2 . 6 

2.4 

2.5 

2.5 

2 . 6 

2.5 

2.5 

2 . 4 

2.6 

2 .4 

2.4 

2 . 4 

2.4 

2.5 

2.6 

2 .5 

2.4 

2.6 

2.5 

2 . 5 

2.5 

2.4 

2.5 

2.5 

2 . 6 

2.5 

2.6 

2.6 

2 . 5 

2 . 5 

2.5 

2.6 

2 . 6 

2.5 

2 . 5 

2.5 

2 . 5 

2 . 4 

Stk 0 2 

• 

0 - 25 

13. 4 0 

13 .4 1 

13 .4 0 

13.40 

13 .4 0 

13 . 39 

13 . 38 

13 .40 

13 .40 

13 .41 

13. 4 1 

13. 4 1 

13 .4 0 

13 . 4 2 

13 .42 

13 . 4 1 

13.39 

13 . 39 

13 .40 

13.39 

13.40 

13. 4 0 

13.3 9 

13 .40 

13 . 41 

13 .41 

13 .41 

13.40 

13. 4 0 

13.39 

13 .39 

13 . 40 

13 . 4 0 

13 . 40 

13 .4 0 

13.40 

13 . 39 

13.40 

13 .39 

13 .39 

02/01/2013 16 , 10 

NOx Mass 

Ib/hr 

0-100 

5 . 11 

5 . 10 

5.84 

5.11 

5.11 

5 . 11 

5 .84 

5.10 

5 . 10 

5.09 

5.82 

5 . 08 

5 . 09 

5.08 

5 . 09 

5 . 09 

5.83 

5 . 10 

5.09 

5.84 

5.08 

5.08 

5.10 

5.07 

5.08 

5.09 

5 . 80 

5.07 

5.80 

5.80 

5 . 08 

5.06 

5.07 

5.79 

5 . 80 

5.07 

5.09 

5.07 

5.07 

5 . 08 

StkFlow 

ksefh 

0 - 300000 

17715 

17697 

17707 

1 7704 

17723 

17691 

17677 

17684 

17681 

17657 

1 7 679 

17648 

17646 

1767 2 

17695 

17665 

17672 

17659 

17645 

17697 

17626 

17629 

17646 

17586 

17622 

17656 

17633 

17571 

17593 

17566 

17577 

17559 

17576 

17580 

17591 

17585 

17642 

17596 

17571 

17586 

G12-C3 G12 - C13 G12 -C10 G12 -C6 G12-C7 G12-C8 G12 - C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2 >Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0 - 1000 

1.6 

1.7 

1.6 

1.7 

1.9 

2 . 0 

1.2 

1.1 

1.3 

1.3 

1. 2 

1.0 

1.0 

1.1 

1.3 

1.1 

1.3 

1.4 

1.1 

1.0 

0.8 

0.9 

0.8 

0.8 

0.7 

0.6 

0.6 

0.6 

0 . 6 

0 . 6 

0.6 

0 . 5 

0.4 

0.4 

0.4 

0 . 3 

0.3 

0.2 

0.1 

0.2 

CO Mass 

Ib/hr 

0 - 100 

2.19 

2.18 

2 . 19 

2.19 

2.19 

2 . 92 

1.46 

1.46 

1.46 

1.45 

1. 45 

1.45 

1. 4 5 

1. 4 5 

1. 4 5 

1. 45 

1.46 

1.46 

1.45 

1.46 

0.73 

1. 45 

0 . 73 

0.72 

0.73 

0 . 73 

0 . 73 

0 . 72 

0.72 

0.72 

0.73 

0.72 

0.7 2 

0 . 72 

0.72 

0.72 

0 . 73 

0.00 

0 . 00 

0.00 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.008 

0.007 

0 . 007 

0.007 

0.008 

0 . 007 

0.007 

0.007 

0.008 

0 . 007 

0.007 

0.007 

0 . 007 

0 . 007 

0.008 

0 . 007 

0 . 007 

0.008 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

0.007 

0 . 008 

0 . 007 

0.008 

0 . 008 

0.007 

0 . 007 

0.007 

0.008 

0 . 008 

0.007 

0.007 

0.007 

0.007 

0 . 007 

Stk NOXc 

ppm 

0-300 

1. 97 

1. 89 

2.05 

1. 89 

1. 97 

1. 96 

2.04 

1. 97 

1. 97 

1. 89 

2.05 

1. 89 

1. 89 

1. 89 

1. 89 

1. 97 

2.04 

1. 96 

1. 89 

2.04 

1. 97 

1. 97 

1.96 

1. 89 

1. 97 

1. 97 

2 .05 

1. 97 

2 . 05 

2.04 

1.96 

1. 97 

1. 97 

2 .05 

2 . 05 

1. 97 

1. 96 

1. 97 

1. 96 

1. 89 

Stk CDc Gas hsefh 

hsefh 

0-10000 

ppm 

0-1000 

1. 2 6 

1. 34 

1. 26 

1. 34 

1. 49 

1. 57 

0.94 

0.87 

1. 02 

1. 02 

0 . 95 

0.79 

0.79 

0.87 

1. 03 

0.87 

1. 02 

1.10 

0.87 

0.79 

0 . 63 

0.71 

0 . 63 

0 . 63 

0.55 

0.47 

0.47 

0.47 

0. 4 7 

0.47 

0.47 

0.39 

0 . 31 

0.31 

0 . 31 

0.24 

0.24 

0.16 

0.08 

0.16 

6951. 0 

6934.8 

694 8.0 

6946 . 8 

6954.0 

6951.0 

6954 . 6 

6939.0 

6937 . 8 

6919.2 

6927.6 

6915 . 6 

6924. 0 

6915.6 

6924.6 

692 2 .2 

6943.2 

6938.4 

6923.4 

6953.4 

6916 . 2 

6917.4 

6933.0 

6900.6 

6905.4 

6918.6 

6909.6 

6894.6 

6903 . 0 

6901.8 

6 906 . 0 

6889.8 

6896 .4 

6898.2 

6902.4 

6900.0 

6931.8 

6904 . 2 

6903.6 

6909.6 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110 . 0 

110.0 

1 1 0.0 

110 . 0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

1 1 0 . 0 

1 10.0 

110.0 

2>Summary - I - Min RATA - Continued 

MW Lo 

0 - 1 

79. ! 

79. 

79. 

79 .. 

79 . . 

79 . 

79 . 

79 .. 

79. ! 

79 . 

79 .. 

79. : 

79. : 

79 . . 

79 . : 

79 .. 

80. ( 

79 . : 

79. ! 

80. ( 

79 .. 

79 . . 

79 . 

79 . . 

79. : 

79. ! 

79 . . 

79 . . 

79. : 

79. : 

79. : 

79 . 

79. : 

79. : 

79 . : 

79 .. 

79 . . 

80. ( 

79 .. 

79 

PagE 
Group# - Channel# 

Long Des crip . 

Short Descrip . 

Units 

Range 

02/01/2013 12 : 01 

02/01/2013 12:02 

02/01/2013 12:03 

02/01/ 2013 12:04 

02/01/2013 12:05 

02/01/ 2 013 12:06 

02/01/ 2 013 12:07 

02/01/2013 12:08 

02/01/2013 12:09 

02/01/2013 12:10 

02/01/2013 12:11 

02/01/2013 12 :12 

02 /01/2013 12:13 

02/01/2013 12:14 

02/01/2013 12:15 

02/01/2013 12 : 16 

02/01/2013 12:17 

02 /01/2013 12 : 18 

02/01/2013 12:19 

02/01/2013 12:20 

02/01/2013 12:21 

02/01/2013 1 2 :22 

Period Average 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed : 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2.4 

2.5 

2.5 

2.5 

2.6 

2.5 

2.3 

2.4 

2.4 

2.5 

2.3 

2.3 

2.4 

2.4 

2.4 

2 . 3 

2.4 

2.4 

2.3 

2.3 

2.3 

2.3 

4.1 

133.7 

0.0 

G12 -C4 G12-Cll G12-C20 

2>stk 0 2 2>NOx Mass 2>StkFlow 

stk 02 

, 

0-25 

13 .40 

13 . 38 

13 .38 

13.39 

13 . 38 

13.38 

13.40 

13 . 39 

13.39 

13 . 37 

13 .39 

13 . 40 

13 .39 

13 .38 

13.38 

13 . 39 

13 . 38 

13 . 39 

13.40 

13.40 

13 .4 0 

13 . 40 

13 .19 

2 2 .46 

0.04 

NOx Mass 

Ib/hr 

0-100 

5.07 

5.09 

5.08 

5.09 

5.82 

5.11 

5.11 

5 . 11 

5.10 

5.12 

5.11 

5.10 

5.10 

5.09 

5.09 

5 . 09 

5 . 11 

5 . 09 

5.09 

5.08 

5.08 

5.09 

6.41 

100.00 

0.00 

StkFlow 

kscfh 

0-300000 

17568 

17589 

17566 

17629 

17618 

17683 

17703 

17708 

17655 

17689 

17696 

17694 

1764 6 

17616 

17619 

17636 

17654 

17642 

17632 

17623 

17622 

17638 

18349 

300000 

o 

G12 -C3 G12 -C13 G12-CI0 G12-C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0-1000 

0.2 

0 . 2 

0.2 

0.1 

0 . 2 

0.1 

0.2 

0 . 2 

0.2 

0.1 

0.2 

0 . 2 

0.2 

0.2 

0 . 2 

0 . 2 

0.2 

0.2 

0.2 

0.2 

0.2 

0.2 

11. 6 

893.5 

0.0 

CO Mass 

lb/hr 

0-100 

0.00 

0 . 00 

0 . 00 

0 . 00 

0 . 00 

0.00 

0.00 

0 . 00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0 . 00 

0.00 

0.00 

2 . 69 

100.00 

0.00 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0 . 007 

0.007 

0.007 

0 . 008 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.009 

0.139 

0 . 000 

Stk NOXc 

ppm 

0-300 

1. 89 

1. 96 

1. 96 

1. 96 

2 . 04 

1. 96 

1. 81 

1. 89 

1. 89 

1. 96 

1. 81 

1. 81 

1. 89 

1. 88 

1. 88 

1. 81 

1. 88 

1. 89 

1. 81 

1. 81 

1. 81 

1. 81 

2. 4 4 

37.85 

0.00 

stk COc Gas 

ppm 

0 - 1000 

0.16 

0 . 16 

0 . 16 

0.08 

0.16 

0.08 

0.16 

0.16 

0.16 

0.08 

0.16 

0.16 

0.16 

0.16 

0.16 

0 . 16 

0 . 16 

0.16 

0 . 16 

0.16 

0.16 

0.16 

4 .02 

252.96 

0.00 

hscfh 

hscfh 

0-10000 

6893.4 

6919.8 

6910.8 

6926.4 

6931.2 

6957.0 

6946.2 

6957 . 6 

6936.6 

6968.4 

6952.8 

6942.6 

6933 . 0 

6930.6 

6931.8 

6929 . 4 

694 5.6 

6931.8 

6918.6 

6915.0 

6914.4 

6921.0 

6922.9 

7024.2 

6862.2 

NH3Inj 

lb/hr 

0-1000 

110 . 0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

MW Lo 

0-1 

79 . ~ 

80.1 

79. : 

79 .. 

80.1 

80.: 

80.1 

80. : 

79. : 

80 .. 

80. ! 

80.: 

79. : 

80 .. 

BO 

80.: 

BO 

80.: 

80.1 

80.1 

79 . 

BO. 

79.8 

Bl. 

7B. 

1.0264E+3 3.3240E+3 1.6154E+3 4.6238E+6 2.9187E+3 6 . 7678E+2 2.22 4 9E+0 6.15 4 7E+2 1.0121E+3 1.744 5E+6 2 . 7720E+4 2 .0124E+ 

100 . 0 100 . 0 100.0 100.0 100.0 100 . 0 100.0 100.0 100.0 100.0 100.0 100 . 

02/01/2013 16 , 10 2>Summary - I - Min RATA - Continued PagE 
Data Summary Report 

Company: CPV Sentinel, LLC 

62575 Powerline Road 

z 

Desert Hot Springs, CA 92240 

5e..t\+:~\ \)";+ 

9M -1t~ Source: 

Data Group: 

Report Name: 

Start of Report: 

Turbine 2 

2 >1 - Min Cales 

2>Summary - I-Min RATA 

01/30/2013 09,26 

G12-C4 

7- 2 (7Tf£ -I'M- /00 - I 

End of Report , 01/30/2013 13,34 

GI2 -CII GI2-Cl3 

TRACE 

Ellvironmelltal Systems, Illc. 

Validation : All Available Data 

Group#-Channel# GI2-ClO G12 -C6 G12-C7 G12-C8 

Long Descrip. 

Short Descrip. 

Units 

G12 - C2 

2:>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

G12 - C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

GI2-C) 

2>Stk CO 

Stk co 

ppm 

0-1000 

2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk CDc 2>Gas Flow 

G12 - C18 

2>NH3 Inj 

NH3Inj 

lb/hr 

0 - 1000 

G12-C 

2>MW Lo 

MW Lo 

Range 

01/30/2013 09:26 

01/30/ 2013 09:27 

01/30/2013 09:28 

01/30/2013 09:29 

01/30/2013 09:30 

01/30/2013 09:31 

01/30/2013 09:32 

01/30/2013 09:33 

01/30/2013 09:34 

01/30/2013 09:35 

01/30/2013 09:36 

01/30/2013 09:37 

01/30/2013 09:38 

01/30/2013 09:39 

01/30/2013 09:40 

01/30/2013 09:41 

01/30/2013 09:42 

01/30/2013 09:43 

01/30/2013 09:44 

01/30/2013 09:45 

01/30/2013 09:46 

0 1 /30/2013 09:47 

01/30/2013 09:48 

01/30/2013 09:49 

01/30/2013 09:50 

01/30/2013 09:51 

01/30/2013 09;52 

01/30/2013 09:53 

01/30/2013 09:54 

01/30/2013 09:55 

Date/Time Printed: 

2.7 

2.8 

2.8 

2.9 

2.8 

2.7 

2.7 

2.8 

2.8 

2.7 

2.7 

2 .8 

2.8 

2.8 

2.8 

2.8 

2.9 

2.9 

2.9 

2.9 

2.9 

2 . 8 

2.9 

2.8 

2.9 

2.8 

2.8 

2.8 

2.8 

2.8 

Stk 02 

% 

0-25 

13.03 

13.02 

13.03 

13.03 

13.04 

13 .04 

13 . 03 

13.03 

13.04 

13.04 

13.04 

13.02 

13.02 

13.03 

13.03 

13.03 

13.02 

13.02 

13.02 

13.03 

13.02 

13 .03 

13 .03 

13.03 

13.03 

13.03 

13.03 

13.04 

13.04 

13.04 

01/30/2013 17,58 

NOx Mass 

Ib/hr 

0-100 

6.21 

7.09 

7.05 

7.04 

7.03 

6.16 

6.1S 

7.07 

7.09 

6.21 

6.22 

7.12 

7.12 

7.10 

7.12 

7.11 

7.12 

7.11 

7.11 

7.11 

7.11 

7.11 

7.10 

7.11 

7.12 

7.13 

7.12 

7.11 

7.12 

7.11 

20518 

20469 

20378 

20362 

20362 

20381 

20426 

20451 

20524 

20553 

20578 

20572 

20549 

20541 

20576 

20566 

20553 

20537 

20525 

20551 

20533 

20563 

20531 

20565 

20594 

20618 

20600 

20588 

20605 

20597 

0.2 

0.1 

0.1 

0.1 

0.1 

0.1 

0.1 

0.1 

0.1 

0.2 

0.2 

0.2 

0 .1 

0.1 

0.1 

0.2 

0.2 

0.2 

0.1 

0.1 

0.2 

0.2 

0.2 

0.2 

0.2 

0.3 

0.3 

D.' 

0.5 

0.5 

CO Mass 

Ib/hr 

0-100 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0 .00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 

0.89 

0.89 

0.89 

0.89 

0.89 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.008 

0.008 

0 . 008 

O.OOS 

0.007 

0.007 

0.008 

0.008 

0.007 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

Stk NOXc 

ppm 

0-300 

2.02 

2.10 

2.10 

2.17 

2.10 

2.03 

2.02 

2.10 

2.10 

2.03 

2.03 

2 . 10 

2.10 

2.10 

2.10 

2.10 

2.17 

2.17 

2.17 

2.17 

2.17 

2.10 

2.17 

2.10 

2.17 

2.10 

2.10 

2.10 

2.10 

2.10 

Stk COe Gas hscfh 

ppm 

0-1000 

0.15 

0 . 07 

0.07 

0.07 

0.08 

0.08 

0.07 

0.07 

0.08 

0.15 

0.15 

0.15 

0.07 

0.07 

0.07 

0.15 

0.15 

0.15 

0.07 

0.07 

0.15 

0.15 

0.15 

0.15 

0.15 

0. 22 

0.22 

0 . 30 

0.38 

0.38 

hscfh 

0-10000 

8448.0 

8438.4 

8390.4 

8383.8 

8373.0 

8380.8 

8410.2 

8420.4 

8439.6 

8451.6 

8461.8 

8481. 0 

8471. 4 

8457.6 

8472.0 

8467.8 

8473.2 

8466.6 

8461.8 

8461.8 

8464.8 

8466.6 

8453.4 

8467.2 

8479.2 

8489.4 

8481.6 

8466.0 

8473.2 

8469.6 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

llO.O 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

llO.O 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

llO.O 

0-1 

102. : 

102.: 

102. 

103.1 

102. : 

102. 

102 

102 .. 

102 .. 

103 

103 .. 

103 . . 

103. ! 

103.1 

103. ! 

103. : 

103 . ! 

103. ! 

103.1 

103.1 

102. : 

103. : 

103.1 

103.1 

102. : 

103. ! 

103. : 

102 . : 

102 

102 . . 

pagE 
Group#-Channel# 

Long Deserip. 

Short Descrip . 

Units 

Range 

01/30/2013 09:56 

01/30/2013 09:57 

01/30/2013 09:58 

01/30/2013 09:59 

01/30/2013 10:00 

01/30/2013 10:01 

01/30/2013 10:02 

01/30/2013 10:03 

01/30/2013 10:04 

01/30/2013 10:05 

01/30/2013 10:06 

01/30/2013 10:07 

01/30/2013 10:08 

01/30/2013 10:09 

01/30/2013 10:10 

01/30/2013 10:11 

01/30/2013 10 : 12 

01/30/2013 10:13 

01/30/2013 10:14 

01/30/2013 10:15 

01/30/2013 10:16 

01/30/2013 10:17 

01/30/2013 10:18 

01/30/2013 10:19 

01/30/2013 10:20 

01/30/2013 10:21 

01/30/2013 10:22 

01/30/2013 10:23 

01/30/2013 10:24 

01/30/2013 10:25 

01/30/2013 10:26 

01/30/2013 10:27 

01/30/2013 10 :2 8 

01/30/2013 10:29 

01/30/2013 10 : 30 

01/30/2013 10:31 

01/30/2013 10:32 

01/30/2013 10:33 

01/30/2013 10:34 

01/30/2013 10:35 

Date/Time Printed: 

G12-C2 G12-C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.7 

2.8 

3.0 

2.9 

2.8 

2.9 

2.9 

2.9 

2.9 

2.9 

2.8 

2.6 

2.9 

3.0 

3.1 

3.1 

3.1 

3.1 

3.1 

3.1 

3.0 

3 . 0 

3.0 

3.0 

3 . 0 

2.9 

2.9 

2.9 

3.1 

3.1 

3.1 

3.0 

3.0 

3.1 

3.0 

2.9 

3.0 

3.1 

3.0 

3 . 0 

Stk 02 

• 

0-25 

13 . 04 

13.03 

13.03 

13.03 

13.03 

13.03 

13.03 

13 .0 5 

13.05 

13.05 

13 . 04 

13.05 

13.03 

13 . 02 

13.01 

13 . 01 

13.00 

13.01 

13 . 02 

13.02 

13.02 

13.03 

13.03 

13.01 

13.02 

13.01 

13.01 

13.01 

13.00 

13.00 

13 . 00 

13.00 

13.01 

13 .01 

13.02 

13.01 

13.00 

13.00 

13.01 

13.01 

01/30/2013 17,58 

NOx Mass 

Ib/hr 

0 - 100 

6.22 

7.12 

7.12 

7.10 

7.12 

7.12 

7.12 

7.11 

7 . 10 

7.10 

7.03 

6.22 

7.12 

7.14 

8.03 

8.04 

8.04 

8 . 02 

8.02 

8.02 

7.13 

7.13 

7.14 

7.14 

7 . 15 

7.15 

7.15 

7.13 

8.01 

8.03 

8.03 

7.14 

7.11 

8.03 

7.13 

7.13 

7.13 

8.03 

7 . 13 

7.12 

StkFlow 

ksefh 

0-300000 

20592 

20585 

20589 

20534 

20572 

20595 

20595 

20601 

20585 

20585 

20362 

20601 

20598 

20616 

20592 

20611 

20584 

20566 

20591 

20585 

20602 

20620 

20632 

20597 

20642 

20614 

20614 

20566 

20514 

20549 

20571 

20553 

20512 

20576 

20586 

20562 

20530 

20556 

20560 

20546 

G12-C3 G12 -C13 G12 - C10 G12-C6 G12-C7 G12-C8 G12 -C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

a .• 

0.5 

a .• 

a .• 

0.4 

a .• 

0 . 3 

a .• 

a .• 

a .• 

0.1 

1.1 

3.5 

3.9 

3.7 

3.7 

3 . 7 

3.6 

3.5 

3.5 

3.5 

3.6 

3.6 

3.5 

3.' 

3.' 

3.6 

3 . 7 

3.7 

3.8 

3.6 

3.3 

3.' 

3.5 

3.7 

3 . 8 

3.6 

3.4 

3.' 

3.5 

CO Mass 

Ib/hr 

0-100 

0.89 

0.89 

0.89 

0.89 

0.89 

0 . 89 

0 .8 9 

0.89 

0 . 89 

0.89 

0.00 

1. 78 

5.34 

6.25 

5.36 

5.36 

5.36 

5.35 

5.35 

5.35 

5.35 

5.35 

5.35 

5.36 

5.36 

5.36 

5.36 

5.35 

5.34 

5 .3 5 

5.36 

5.35 

5.33 

5 . 35 

5.35 

5 . 35 

5 . 35 

5.35 

5.35 

5.34 

NOx Rate 

lb/mrnBtu 

0-1 

0.007 

0 . 008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.009 

0.009 

0.009 

0.009 

0.009 

0.009 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0.009 

0.009 

0.009 

0.008 

0 . 008 

0.009 

0.008 

0 . 008 

0.008 

0.009 

0.008 

0.008 

Stk NOXe 

ppm 

0-300 

2.03 

2.10 

2.25 

2.17 

2.10 

2.17 

2.17 

2.18 

2.18 

2.18 

2.10 

1. 95 

2.17 

2.25 

2.32 

2.32 

2 . 32 

2.32 

2.32 

2.32 

2.25 

2.25 

2.25 

2.24 

2.25 

2.17 

2.17 

2.17 

2.32 

2.32 

2.32 

2.24 

2 .2 4 

2.32 

2.25 

2.17 

2.24 

2.32 

2.24 

2.24 

Stk COe Gas hsefh 

hsefh 

0 - 10000 

ppm 

0-1000 

0.30 

0.37 

0.30 

0.30 

0.30 

0.30 

0.22 

0.30 

0.30 

0.30 

0.08 

0.83 

2.62 

2.92 

2.77 

2.77 

2.76 

2.69 

2.62 

2.62 

2.62 

2.70 

2.70 

2.62 

2.55 

2.54 

2.69 

2.77 

2.76 

2.84 

2.69 

2.46 

2.54 

2.62 

2.77 

2.84 

2.69 

2.54 

2.54 

2.62 

8467.8 

8475.6 

8477.4 

8454.6 

8470.2 

8479.8 

8479.8 

8460.6 

8454.0 

8454.0 

8373.0 

8460 . 6 

8481.0 

8499.0 

8500.2 

8508.0 

8507.4 

8489.4 

8488.8 

8486.4 

8493.6 

8490.0 

8494.8 

8502.0 

8509.8 

8509.2 

8509.2 

8489 4 

8478.6 

8493.0 

8502.0 

8494.8 

8467.2 

8493.6 

8487.0 

8487.6 

8485.2 

8496.0 

8487.0 

8481.0 

NH3Inj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - 1-Min RATA - Continued 

MW Lo 

0-1 

102 .. 

102. : 

102. : 

102.: 

102 .. 

102. 

103.l 

102. 

102. 

102. : 

102. : 

102. 

102.: 

102. : 

103.: 

103. I 

103. : 

103.l 

103 . ~ 

103.l 

103.1 

103 

103. 

103. : 

103. : 

103. 

103. : 

103. 

103.1 

103.1 

103 . 

103. ! 

102 .. 

103 

103.: 

103.: 

103.l 

103 .. 

102. : 

102 

PagE 
Group#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

01/30/2013 10;36 

0 1 /30/2013 10:37 

01/30/2013 10:38 

01/30/2013 10 : 39 

01/30/2013 10;40 

0 1 /30/2013 10:41 

01/30/2013 10:42 

01/30/2013 10;43 

01/30/2013 10:44 

01/30/2013 10;45 

01/30/2013 10;46 

01/ 30 /2013 10:47 

01/30/2013 10;48 

01/30/2013 10:49 

01/30/2013 10:50 

01/30/2013 10;51 

01/30/2013 10;52 

01/30/2013 10:53 

01/30/2013 10;54 

01/30/2013 10:55 

01/30/2013 1 0:56 

01/30/2013 10;57 

01/30/2013 10:58 

01/30/2013 10:59 

01/30/2013 11:00 

01/30/2013 11:01 

01/ 30 /2013 11:02 

01/30/2013 11:03 

01/30/2013 11:04 

01/30/2013 11:05 

01/30/2013 11:06 

01/30/2013 11;07 

01/30/2013 11:08 

0 1 /30/2013 11:09 

01/30/2013 11 ;10 

01/30/2013 11;11 

01/30/2013 11:12 

01/30/ 20 13 11:13 

01/30/2013 11:14 

01/30/2013 11:15 

Date/Time Printed: 

GI2 -C2 G12-C4 G12-Cll 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

3.0 

3.0 

3.0 

3.0 

3.0 

2.9 

3.0 

3.1 

3.0 

3.1 

3.1 

3.1 

3.0 

3.0 

3.0 

3.1 

3.0 

3.0 

3.0 

3.0 

3.0 

3.0 

3.0 

3.0 

2.9 

3.0 

2.9 

3.0 

3.0 

3.0 

3.0 

3.0 

3.0 

2.8 

3.0 

2.9 

2.8 

2.8 

3.0 

2.8 

Stk 02 

• 

0 -2 5 

13.00 

13.02 

13.01 

13.01 

13.01 

13. 01 

13.01 

13. 01 

13.02 

13.01 

13.02 

13. 01 

13.01 

13.01 

13 .00 

13.01 

13. 0 1 

13.02 

13.03 

13. 02 

13.02 

13.02 

13.02 

13.03 

13.03 

13.02 

13.02 

13.02 

13.03 

13 .01 

13 . 0 2 

13.03 

13.03 

13.04 

13.03 

13.04 

13.05 

13.05 

13.04 

13.05 

01/30/2013 17,58 

NOx Mass 

1b/hr 

0-100 

7.13 

7.11 

7.11 

7.13 

7.12 

7.12 

7.13 

8 .03 

7.12 

8.00 

7.99 

8.02 

7.12 

7.13 

7.13 

8.01 

7.11 

7.11 

7.09 

7.13 

7.12 

7.12 

7.11 

7.10 

7.10 

7.11 

7.10 

7.10 

7.11 

7.12 

7.10 

7.10 

7.09 

7.09 

7.10 

7 .08 

7.07 

7.06 

7.06 

7.05 

G1l-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20533 

20531 

20502 

20555 

20537 

20524 

20576 

20579 

20550 

20521 

20514 

20559 

20540 

20560 

20534 

20534 

20508 

20518 

20500 

20578 

20553 

20572 

20530 

20532 

20514 

20528 

20492 

20506 

20544 

20546 

20511 

20525 

20505 

20532 

20540 

20496 

20493 

20478 

20 427 

20434 

G1l - C3 

2>Stk CO 

Stk co 

ppm 

0-1000 

3.5 

3.4 

3.4 

3.4 

3.5 

3 .3 

3.4 

3.5 

3 .5 

3.4 

3.2 

3.2 

3.3 

3.4 

3.5 

3.3 

3.' 

3.2 

3 .3 

3.1 

3.2 

3.2 

3.2 

3.2 

3.2 

3.2 

3.3 

3.2 

3.3 

3.2 

3.2 

3.2 

3 . 0 

3.1 

3.1 

3.2 

3 . 3 

3.6 

3.4 

3.1 

G12 -C13 G12-CIO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

1b/hr 

0-100 

5.35 

5.33 

5.33 

5.35 

5.34 

5 .34 

5.35 

5.35 

5.34 

5.34 

4.44 

4.46 

5.34 

5.35 

5.35 

5.34 

5.33 

4 .44 

5.32 

4.45 

4.4 5 

4.45 

4.44 

4.44 

4.43 

4.44 

5.32 

4.44 

5.33 

4 .45 

4.44 

4.44 

4.43 

4.43 

4 .4 4 

4.4 3 

5.30 

5.30 

5.29 

4 . 41 

NOx Rate 

lb/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.009 

0.008 

0.009 

0.009 

0.009 

0.008 

0.008 

0.008 

0.009 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

Stk NOXc 

ppm 

0-300 

2.24 

2.25 

2.24 

2.24 

2.24 

2.17 

2.24 

2.32 

2.25 

2.32 

2.32 

2.32 

2.24 

2.24 

2.24 

2.32 

2.24 

2.25 

2 . 25 

2.25 

2.25 

2.25 

2.25 

2.25 

2.17 

2.25 

2.17 

2.25 

2.25 

2.24 

2.25 

2.25 

2.25 

2.10 

2.25 

2.18 

2. 10 

2.10 

2.25 

2.10 

G12 -C7 G12 -C8 

2>Stk COc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

2.61 

2.55 

2.54 

2.54 

2.62 

2.47 

2.54 

2.62 

2.62 

2.54 

2 . 40 

2.39 

2.47 

2.54 

2.61 

2.47 

2.54 

2.40 

2 .4 7 

2 .32 

2.40 

2.40 

2.40 

2.40 

2.40 

2.40 

2.47 

2.40 

2.47 

2.39 

2 .40 

2.40 

2.25 

2.33 

2.32 

2.40 

2.48 

2. 71 

2.55 

2.33 

8486.4 

8464.2 

8463.0 

8484.6 

8477.4 

8472.0 

8493.6 

8494.8 

8472.0 

8470.8 

8457.0 

8486.4 

8478.6 

8487.0 

8487.0 

8476.2 

8465.4 

8458.8 

8440.8 

8483.4 

8473.2 

8481.0 

8463.6 

8454.0 

8446.2 

8463.0 

8448.0 

8454.0 

8458.8 

8481.0 

8455.8 

8451.0 

84 4 2.6 

84 4 3.2 

8457.0 

8428.2 

8416.2 

8410.2 

8400.0 

83 92.2 

G12-C18 

2 >NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

11 0.0 

110.0 

110 .0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

11 0.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW La 

MW Lo 

0-1 

103.! 

103 

102.' 

103. ! 

102.' 

103. ! 

103 . . 

102. : 

102 .. 

102 . . 

102 . . 

103 

103. : 

103 .• 

102. : 

103. : 

102 . 

102.J 

102 .. 

102. : 

102 . 

103 . . 

103. ! 

10 3 . . 

10 2. : 

102 .. 

102.: 

103.: 

102 .. 

103. 

102. : 

103.1 

102 .. 

103. 1 

102 . : 

10 2 . : 

102 . 

102. : 

102 . . 

101 . . 

Pag~ 
Group#-Channel# 

Long Descrip . 

Short Descrip. 

Units 

Range 

01/30/2013 11:16 

01/30/2013 11:17 

01/30/2013 11:18 

01/30/2013 11:19 

01/30/2013 11:20 

01/30/2013 11:21 

01/30/2013 11:22 

01/30/2013 11:23 

01/30/2013 11:24 

01/30/2013 11:25 

01/30/2013 11:26 

01/30/2013 11:27 

01/30/2013 11:28 

01/30/2013 11:29 

01/30/2013 11:30 

01/30/2013 11:31 

01/30/2013 11:32 

01/30/2013 11:33 

01/30/2013 11:34 

01/30/2013 11:35 

01/30/2013 11:36 

01/30/2013 11:37 

01/30/2013 11:38 

01/30/2013 11:39 

01/30/2013 11:40 

01/30/2013 11 :4 1 

01/30/2013 11:42 

01/30/2013 11:43 

01/30/2013 11 :44 

01/30/2013 11:45 

01/30/2013 11:46 

01/30/2013 11:47 

01/30/2013 11:48 

01/30/2013 11:49 

01/30/ 2013 11:50 

01/30/2013 11:51 

01/30/2013 11:52 

01/30/2013 11:53 

01/30/2013 11:54 

01/30/2013 11 , 55 

Date/Time Printed : 

G12-C2 G12-C4 G12 -Cll G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

3.0 

2.8 

3 . 1 

2.8 

2.9 

2.8 

2 . 9 

2 . 9 

2.9 

2.8 

2.9 

3.0 

2.9 

2.9 

2.9 

3.0 

2.9 

2.9 

2.8 

3.0 

3.0 

2.9 

3.0 

3.0 

3.1 

3 . 0 

2.9 

2.9 

2.9 

2.9 

3.0 

3.0 

2.9 

2.9 

2.9 

2.9 

2.9 

2.9 

3.0 

3.0 

Stk 02 

% 

0-25 

13.04 

13.05 

13 . 02 

13.04 

13.05 

13 . 06 

13.06 

13 . 05 

13.04 

13 . 03 

13.03 

13 . 02 

13 . 03 

13.02 

13.03 

13.03 

13.03 

13.02 

13.02 

13.02 

13.02 

13 . 02 

13.01 

13 . 02 

13.00 

13 . 00 

13.01 

13.01 

13.01 

13.02 

13.01 

13 . 02 

13.02 

13 . 02 

13 . 02 

13.02 

13.02 

13.01 

13.00 

13.00 

01/30/2013 17,58 

NOx Mass 

lb/hr 

0-100 

7.06 

7.07 

7.96 

7.05 

7.08 

7 . 07 

7 . 08 

7.08 

7.08 

7.09 

7.09 

7.10 

7.08 

7.0B 

7.06 

7.0B 

7.07 

7.09 

7.09 

7.09 

7.09 

7.09 

7.08 

7.0B 

7.99 

7.10 

7.0B 

7.09 

7.0B 

7.0B 

7.07 

7.0B 

7.0B 

7.06 

7.07 

7.07 

7.06 

7.06 

7.08 

7.09 

StkFlow 

kscfh 

0-300000 

20430 

204B3 

20425 

20419 

20515 

20512 

20541 

20516 

20494 

204B6 

20499 

204B7 

20476 

20435 

20409 

20463 

2044B 

20479 

20476 

20485 

20476 

20469 

20432 

20457 

20465 

20439 

20415 

20437 

20421 

20451 

20389 

20 44 1 

20434 

20393 

20407 

20428 

203B4 

2 0371 

20380 

20409 

G12-C3 G12-C13 G12-CI0 G12 - C6 G12 - C7 G12 -C8 G12 -C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk co 

ppm 

0-1000 

3.2 

2.9 

3 . 4 

2.4 

3.5 

3.7 

3.7 

3.5 

3.0 

3.0 

2.9 

2.9 

2.8 

2 . 8 

3.0 

2.9 

2 . 8 

2.8 

2.8 

2.7 

2.8 

2.8 

2.8 

2.8 

2.7 

2.8 

2.8 

2.7 

2.7 

2.9 

2 . 8 

2.7 

2 . 7 

2.8 

2.7 

2.8 

2.8 

2.8 

2.7 

2.7 

CO Mass 

lb/hr 

0-100 

4.41 

4.42 

5.30 

3 . 53 

5.31 

5.30 

5.31 

5.31 

4.42 

4.43 

4.43 

4.43 

4.43 

4. 42 

4.41 

4.42 

4.42 

4.43 

4.43 

4.43 

4 .4 3 

4.43 

4 .43 

4.43 

4.44 

4.44 

4.42 

4.43 

4.43 

4.43 

4.42 

4.42 

4.42 

4.41 

4.42 

4.42 

4.41 

4.41 

4.42 

4.43 

NOx Rate 

lb/mmBtu 

0-1 

O.OOB 

0.008 

0.009 

O.OOB 

0.008 

O. OOB 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0.008 

0.008 

0 . 008 

0.008 

O.OOB 

0.008 

O.OOB 

0.009 

O. OOB 

O.OOB 

0 . 008 

O.OOB 

O.OOB 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0 . 008 

0.008 

0.008 

Stk NOXc 

ppm 

0-300 

2.25 

2.10 

2.32 

2.10 

2 . 18 

2.11 

2.1B 

2.18 

2 . 18 

2.10 

2.17 

2 .2 5 

2.17 

2.17 

2 . 17 

2 .25 

2.17 

2.17 

2.10 

2.25 

2.25 

2.17 

2.24 

2.25 

2.32 

2 . 24 

2.17 

2.17 

2.17 

2 . 17 

2 .24 

2.25 

2 . 17 

2.17 

2 . 17 

2 . 17 

2.17 

2.17 

2.2 4 

2.24 

Stk COc Gas 

ppm 

0-1000 

hscfh 

hscfh 

0-10000 

2. 4 0 

2.1B 

2.55 

1. 80 

2.63 

2.7B 

2.7B 

2.63 

2.25 

2.25 

2 . 17 

2 . 17 

2.10 

2.10 

2.25 

2.17 

2.10 

2.10 

2.10 

2 . 02 

2.10 

2.10 

2.09 

2.10 

2.02 

2.09 

2.09 

2.02 

2.02 

2.17 

2. 09 

2.02 

2.02 

2.10 

2.02 

2.10 

2.10 

2.09 

2.02 

2.02 

8401.2 

B412 . 0 

8420.4 

B396.4 

8425 . 2 

8413.2 

8 42 5.2 

8425 . 8 

B427 . 6 

8434.8 

B440.2 

B446.2 

8430 .6 

B424.6 

8403.0 

B425.2 

8419.2 

8442.6 

8441.4 

8445.0 

8441.4 

843B.4 

8434.2 

8433.6 

8458.2 

8447.4 

8427.0 

8436 . 0 

8429.4 

8431 .2 

8416.2 

8427.0 

B424 . 0 

B4 07.2 

B413.2 

B421.6 

B403.6 

8409.0 

8423.4 

8435.4 

NH3Inj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

MW Lo 

0-1 

102. 

10 2 .. 

102 . . 

102 . 1 

10 2 . . 

102.1 

102 . 1 

102. ' 

102. : 

102 . 1 

102. : 

102 . . 

102 .. 

102 .. 

102.1 

102. ~ 

102 .. 

102 .. 

102 . ~ 

102. 

102 

102 . . 

102 .. 

102 .. 

102. 

103.1 

102. 

102. J 

102. 

103 .. 

102. : 

102. : 

102 . . 

102. ~ 

102 . . 

102 . . 

102 .. 

102 . ~ 

102 . . 

102 . : 

Pag( 
Group#-Channel# 

Long Descrip . 

Short Descri p . 

Units 

Range 

01/30/2013 11:56 

01/30/2013 11:57 

01/30/2013 11:58 

01/30/2013 11:59 

01/30/2013 12:00 

01/30/2013 12:01 

01/30/2013 12:02 

01/30/2013 12:03 

01/30/2013 12:04 

01/30/2013 12:0S 

01/30/2013 12:06 

01/30/2013 12:07 

01/30/2013 12:08 

01/30/2013 12:09 

01/30/2013 12 , 10 

01/30/2013 12:11 

01/30/2013 12:12 

01/30/2013 12:13 

01/30/2013 12:14 

01/30/2013 12:15 

01/30/2013 12:16 

01/30/2013 12:17 

01/30/2013 12:18 

01/30/2013 12:19 

01/30/2013 12:20 

01/30/2013 12:21 

01/30/2013 12:22 

01/30/2013 12:23 

01/30/2013 12:24 

01/30/2013 12:25 

01/30/2013 12:26 

01/30/2013 12:27 

01/30/2013 12:28 

01/30/2013 12:29 

01/30/2013 12:30 

01/30/2013 12:31 

01/30/2013 12:32 

01/30/2013 12:33 

01/30/2013 12:34 

01/30/2013 12:35 

Date/Time Printed: 

G12 -C2 G12-C4 G12-C11 

2>Stk NOx 

stk NOx 

ppm 

0 -150 

2>Stk 02 2>NOx Mass 

3.0 

3.0 

2 .• 

3.0 

2.' 

3.0 

3.0 

2.' 

2 .• 

2.9 

2.' 

3.0 

2.' 

2.' 

3.0 

2.' 

3.0 

3.0 

2.' 

3.1 

3.1 

3.1 

3.0 

3.1 

3.0 

3.0 

3.0 

3.0 

3.0 

2 .• 

2.' 

3.0 

3.0 

3.0 

2.' 

3.0 

2 .• 

3.0 

3.0 

3.0 

Stk 02 

\ 

0-25 

13.00 

13.01 

13.02 

13.00 

13.01 

13.00 

12.99 

13.01 

13.00 

13.00 

12.99 

13.00 

12.99 

12.99 

12 . 98 

13.00 

12.98 

12.97 

12.98 

12.98 

12.97 

12.97 

12 . 97 

12.96 

12.97 

12.96 

12.97 

12.97 

12.98 

12 . 98 

12.98 

12.97 

12.97 

12.98 

12.98 

12.98 

12.98 

12.96 

12.96 

12.95 

01/30/2013 17,58 

NOx Mass 

lb/hr 

0 - 100 

7.08 

7.09 

7.07 

7.10 

7.09 

7.10 

7.11 

7.10 

7.09 

7.09 

7.09 

7.09 

7.11 

7.10 

7.12 

7.10 

7.13 

7.14 

7.12 

8 .00 

7.14 

7.13 

7.14 

7.15 

7.13 

7.13 

7.13 

7.12 

7.10 

7.10 

7.11 

7.12 

7. 1 2 

7.10 

7.11 

7.09 

7.10 

7.11 

7.13 

7.12 

G12 -C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

2 0401 

20448 

20422 

20456 

20459 

20441 

20462 

20469 

20430 

20431 

20407 

20421 

20440 

20430 

20442 

20460 

20477 

20494 

20456 

20429 

20490 

20447 

20477 

2 0489 

20452 

20429 

20465 

20425 

20387 

20393 

20423 

20428 

20439 

20407 

20440 

20378 

20407 

20377 

20 421 

20385 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

2.7 

2.7 

2 .• 

2.6 

2 .• 

2.6 

2.6 

2.7 

2.6 

2.7 

2.6 

2.7 

2.5 

2.7 

2.' 

2.6 

2.5 

2.5 

2.6 

2.' 

2.6 

2.3 

2.7 

2.5 

2.7 

2.5 

2.7 

2.6 

2 .• 

2.7 

2 .• 

2.6 

2.7 

2.5 

2.7 

2.7 

2.7 

2.7 

2.6 

2.6 

G12-C13 G12-CI0 G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

lb/hr 

0-100 

4.43 

4.43 

4.42 

3.55 

4.43 

3.55 

3.56 

4 . 44 

3.55 

4.43 

3.55 

4.43 

3.55 

4.44 

3.56 

3.55 

3.56 

3.57 

3.56 

3.56 

3.57 

3.56 

4.46 

3.57 

4.45 

3.56 

4.46 

3.56 

4.44 

4.44 

4.44 

3.56 

4.45 

3.55 

4.45 

4.43 

4.44 

3.56 

3.56 

3.56 

NOx Rate 

lb/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.00. 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.00 9 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.00 8 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.00 8 

0.008 

0.008 

Stk NOXc 

ppm 

0-300 

2.24 

2.24 

2.17 

2.24 

2.17 

2.24 

2.24 

2.17 

2.17 

2.17 

2.16 

2.24 

2.16 

2.16 

2.23 

2 . 17 

2.23 

2.23 

2.16 

2.31 

2.31 

2.31 

2.23 

2.30 

2.23 

2.23 

2.23 

2.23 

2.23 

2.16 

2.16 

2.23 

2.23 

2.23 

2.16 

2.23 

2.16 

2.23 

2.23 

2.23 

G12-C7 G12-C8 

2>Stk CDc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 

2.02 

2.02 

2.10 

1. 94 

2. 09 

1. 94 

1. 94 

2.02 

1. 94 

2.02 

1. 94 

2.02 

1. 86 

2 . 01 

1. 79 

1. 94 

1. 86 

1. 86 

1. 94 

1. 79 

1. 93 

1. 71 

2.01 

1. 86 

2.01 

1. 86 

2.01 

1. 93 

2.09 

2.01 

2.09 

1. 93 

2.01 

1. 86 

2.01 

2.01 

2.01 

2 .01 

1. 93 

1. 93 

0-10000 

8431.8 

8440.8 

8419.2 

8454.6 

8445.0 

8448.6 

8467.8 

8449.2 

8443.8 

8444.4 

8445.0 

8440.2 

8458.8 

8454.6 

8470.2 

8456.4 

8484.6 

8502.6 

8476.2 

8464.8 

8500.8 

8482.8 

8495.4 

8511.0 

8485.2 

8486.4 

8490.6 

8473.8 

8447.4 

8449.8 

8462.4 

8475.0 

8479.8 

8455.8 

8469.6 

8443.8 

8455.8 

8464.8 

8482.8 

8478.6 

G12 -C18 

2>NH3 Inj 

NH3Inj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

102. : 

102 

102. : 

103.: 

102 .. 

102 . ~ 

103. : 

102.: 

102 . : 

102. ~ 

102. 

102. 

103.1 

103 .. 

103. 

102 

103 .. 

104.1 

103. 

103. : 

103. 

103. : 

103. : 

103 . . 

103 . . 

103. 

103.: 

103 . ~ 

102. ! 

102. : 

103 .. 

103 . . 

103. : 

103. 

103 .. 

103.1 

103.1 

103 . . 

102 

103 .. 

PagE 
Group#-Channel# 

Long Descrip. 

Short Descrip. 

units 

Range 

01/30/2013 12:36 

01/30/2013 12:37 

01/30/2013 12:38 

01/30/2013 12:39 

01/30/2013 12:40 

01/30/2013 12:41 

01/30/2013 12:42 

01/30/2013 12:43 

01/30/2013 12:44 

01/30/2013 12:45 

01/30/2013 1 2:46 

01/30/2013 12:47 

01/30/2013 12:48 

01/30/2013 12:49 

01/30/2013 12:50 

01/30/2013 12:51 

01/30/2013 12:52 

01/30/2013 12:53 

01/30/2013 12:54 

01/30/2013 12:55 

01/30/2013 12:56 

01/30/2013 12:57 

01/30/2013 12:58 

01/30/2013 12:59 

01/30/2013 13:00 

01/30/2013 13:01 

01/30/2013 13:02 

01/30/2013 13:03 

01/30/2013 13:04 

01/30/2013 13:05 

01/30/2013 13:06 

01/30/2013 13:07 

01/30/2013 13:08 

01/30/2013 13:09 

01/30/2013 13,10 

02/30/2013 1 3:11 

01/30/2013 13:12 

01/30/2013 13:13 

01/30/2013 13:14 

01/30/2013 13:15 

Date/Time Printed: 

G12-C2 G12-C4 G12-C11 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

3.0 

3.0 

2.9 

2.9 

3.0 

3.0 

3.0 

2.9 

3.0 

2.9 

3.0 

3.1 

3.0 

2.9 

2.9 

3.0 

3.0 

3.0 

2.9 

2.9 

2.9 

3.0 

3.0 

3.0 

3.0 

2.9 

3.0 

2.9 

2.9 

2.8 

2.9 

2.9 

2.8 

2.8 

2.8 

2.8 

2.8 

2.9 

2.8 

2.8 

Stk 02 

• 

0-25 

12.96 

12.96 

12.96 

12.96 

12.96 

12.98 

12 .96 

12.98 

12.97 

12.97 

12.97 

12 .95 

12.95 

12.96 

12.96 

12.96 

12.97 

12.97 

12.98 

12.97 

12.97 

12.98 

12.96 

12.96 

12.96 

12.96 

12.95 

12.96 

12.94 

12.94 

12.94 

12.95 

12.97 

12.96 

12.96 

12.96 

12.95 

12.94 

12.96 

12.95 

01/30/2013 17,58 

NOx Mass 

Ib/hr 

0-100 

7.13 

7.13 

7.12 

7.12 

7.12 

7.11 

7.12 

7.10 

7.10 

7.11 

7.11 

7.13 

7.12 

7.11 

7.10 

7.12 

7.09 

7.10 

7.10 

7.11 

7.09 

7.10 

7.12 

7.11 

7.10 

7.09 

7.11 

7.09 

7.13 

7.11 

7.12 

7.10 

7.09 

7.11 

7.11 

7.10 

7.12 

7.13 

7.11 

7.11 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20422 

20427 

20408 

20419 

20392 

20433 

20399 

20401 

20387 

20405 

20402 

20414 

20388 

20389 

20357 

20390 

20355 

20381 

20387 

20396 

20357 

20404 

20396 

20388 

20362 

20314 

20346 

20315 

20378 

20336 

20354 

20324 

20338 

20379 

20388 

20356 

20375 

20384 

20366 

20359 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

2.3 

2.5 

2.4 

2.7 

2.5 

2.7 

2.5 

2.8 

2.7 

2.5 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.5 

2.6 

2.8 

2.6 

2.8 

2.5 

2.6 

2.6 

2.8 

2.9 

2.5 

2.7 

2.7 

2.5 

2.6 

2.5 

2.5 

2.6 

2.5 

2.6 

2.5 

2.6 

2.6 

G12-C13 G12 -C10 G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

3.56 

3.56 

3.56 

3.56 

3.56 

4.45 

3.56 

4.44 

4.44 

3.56 

3.55 

3.57 

3.56 

3.56 

3.55 

3.56 

3.55 

3.55 

3.55 

4.44 

3.55 

4.44 

3.56 

3.56 

3.55 

4.43 

4.44 

3.54 

3.56 

3.56 

3.56 

3.55 

3.54 

3.56 

3.56 

3.55 

3.56 

3.57 

3.55 

3.56 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

Stk NOXC 

ppm 

0-300 

2.23 

2.23 

2.15 

2.15 

2.23 

2.23 

2 .23 

2.16 

2.23 

2.16 

2.23 

2.30 

2.23 

2.15 

2. 15 

2.23 

2.23 

2.23 

2.16 

2.16 

2.16 

2.23 

2.23 

2.23 

2.23 

2.15 

2.23 

2.15 

2.15 

2.08 

2.15 

2.15 

2.08 

2.08 

2.08 

2.08 

2.08 

2.15 

2.08 

2.08 

G12-C7 G12-C8 

2>Stk COc 2>Gas Flow 

Stk CDc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1. 71 

1. 86 

1. 78 

2.01 

1. 86 

2.01 

1. 86 

2.09 

2.01 

1. 86 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.01 

1. 93 

1. 86 

1. 94 

2.08 

1. 93 

2.09 

1. 86 

1. 93 

1. 93 

2.08 

2.15 

1. 86 

2.00 

2.00 

1. 85 

1. 93 

1. 86 

1. 86 

1. 93 

2. 86 

1. 93 

1. 85 

1. 93 

1. 93 

8483.4 

8485.2 

8477.4 

8482.2 

8470.8 

8466.6 

8473.8 

8453.4 

8458.2 

8465.4 

8464.2 

8490.6 

8479.8 

8469.6 

8456.4 

8470.2 

8445.0 

8455.8 

8447.4 

8461.8 

8445.6 

8454.6 

8472.6 

8469.0 

8458.2 

8438.4 

8462.4 

8439.0 

8486.4 

8469.0 

8476.2 

8453.4 

8437. 8 

8465.4 

8469.0 

8455.8 

8474.4 

8488.8 

8460.0 

8467.8 

G12-C18 

2>NH3 Inj 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110 .0 

110 .0 

110 .0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I -Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

103. ! 

103 . . 

103.: 

103.: 

103 

102. 

103. ~ 

103 . : 

102 . . 

103 .. 

103. : 

103. : 

103 .. 

103.1 

103.1 

103 . . 

102 .. 

103.1 

102 . . 

103. 1 

102 .. 

102 .. 

103.1 

103.1 

103 .. 

102. : 

102 .. 

102. 

104.1 

103 .. 

103.1 

103.1 

102 .. 

102 

103. 1 

103 .. 

103 . . 

103 .. 

103.1 

103 .. 

PagE 
Group#-Channel# 

Long Descrip_ 

short Descrip. 

Units 

Range 

01/30/ 2 013 13:16 

01/30/2013 13:17 

01/30/2013 13:18 

01/30/2013 13:19 

01/30/2013 13:20 

01/30/ 2 013 13:21 

01/30/2013 13:22 

01/30/2013 13:23 

01/30/2013 13:24 

01/30/2013 13:25 

01/30/2013 13:26 

01/30/ 2 013 13: 2 7 

01/30/ 2 013 13:28 

01/30/2013 13:29 

01/30/2013 13:30 

01/30/2013 13:31 

01/30/2013 13 : 32 

01/30/ 2 013 13:33 

01/30/2013 13:34 

Period Average 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Pr inted : 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2.7 

2.8 

2.8 

2.8 

2.8 

2.8 

2.8 

2.7 

2 . 8 

2.7 

2.8 

2. 7 

2 .9 

2.9 

2 . 8 

2.9 

2.9 

2.9 

2.9 

2.9 

3.1 

2.6 

G12 -C4 G12 - C11 G12 - C20 

2>Stk 02 2>NOx Mass 2>StkF1ow 

Stk 02 

• 

0-25 

1 2. 96 

12 . 95 

12 . 94 

12 . 94 

12.95 

1 2 .96 

12.96 

12.96 

12 . 96 

12.96 

12 . 96 

12 . 97 

12 . 94 

12.91 

12.93 

12.93 

1 2. 93 

12.92 

12.92 

13.00 

13 . 06 

12.91 

NOx Mass 

Ib/hr 

0 -100 

6.22 

7.10 

7.11 

7.09 

7.10 

7 . 09 

7.08 

6.20 

7.08 

6.20 

7 . 08 

6.19 

7.12 

7 . 16 

7.15 

7.14 

7 . 15 

7.14 

7.14 

7.13 

8.04 

6 . 16 

StkFlow 

kscfh 

0 - 300000 

20360 

20309 

20325 

20274 

20327 

20310 

20304 

20302 

20288 

20317 

20285 

20308 

2 0368 

20395 

20400 

20391 

20414 

20370 

20363 

204 69 

20642 

20274 

G12-C3 G12 -C13 G12 - C10 G12 -C6 G12-C7 G12 - C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW La 

Stk CO 

ppm 

0-1000 

2.8 

2.6 

2.9 

2 . 7 

2.7 

2.7 

2.8 

2 . 8 

2.7 

3.0 

2.7 

2. 9 

2.9 

2.6 

2.8 

2.6 

2.6 

2 .8 

2 . 5 

2 . 5 

3.9 

0 . 1 

CO Mass 

Ib/hr 

0-100 

4.44 

3.55 

4.44 

3.55 

3.55 

3.54 

4 .43 

4.43 

3 . 5 4 

4 . 43 

3.54 

4. 4 2 

4 . 45 

3 . 58 

4.47 

3.57 

3.58 

4. 47 

3.57 

3 . 71 

6 . 25 

0.00 

NOx Rate 

1b/mmBtu 

0-1 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0 . 007 

0 . 008 

0 . 008 

0 . 008 

0 . 008 

0 . 008 

0.008 

0.008 

0.008 

0 . 009 

0 . 007 

Stk NOXe 

ppm 

0-300 

2 . 01 

2 . 08 

2.08 

2 . 08 

2.08 

2.08 

2 . 08 

2.01 

2.08 

2.01 

2 . 08 

2.01 

2.15 

2 . 14 

2.07 

2 . 15 

2 . 15 

2.14 

2.14 

2 . 19 

2.32 

1. 95 

stk CDc Gas hsefh 

ppm hscfh 

0-1000 0 - 10000 

2.08 8457.6 

1.93 8446.8 

2.15 8464.2 

2.00 8443.2 

2.00 8454.6 

2.01 8436.6 

2 . 08 8434 . 2 

2 . 08 8433.6 

2.01 8427.6 

2.23 8439.6 

2.01 8426 . 4 

2.16 8425.2 

2.15 8482 . 2 

1.92 8525 . 4 

2 . 07 8506.2 

1 . 92 8502.6 

1.92 8512 . 2 

2.07 8504.4 

1.85 8501.4 

1.86 8459.2 

2.92 8525.4 

0 . 07 8373 . 0 

NH3Inj 

lb/hr 

0 -1 000 

110.0 

110.0 

110.0 

63 . 2 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

109.8 

110.0 

63.2 

MW Lo 

0-1 

102 

102." 

103 . : 

102.' 

102 . ' 

103 . 1 

102.' 

102. ' 

102.' 

102.' 

102.! 

102 . ' 

103 . 

104.' 

103 . 

103 . 

103.' 

103 . 

103. ' 

102.9 

104 . 

101. 

7 . 2880E+2 3 . 2371E+3 1.7764E+3 5.0968E+6 6.1970E+2 9.2486E+2 2.0000E+0 5.4432E+2 4.6265E+2 2.1063E+6 2.7343E+4 2.5627E+ 

100.0 100.0 100 . 0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100. 

01/30/2013 17,58 2>Summary - 1-Min RATA - Continued Pag( 
Data Summary 

Company : 

So urce : 

Data Group: 

Report Name: 

Start of Report : 

Report csN ~~A1.\ U-.+2 fl ~ 

\<;~5"- \t"'-' 

CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 92240 

Turbine 2 

2>1-Min Cales 

2>Summary - I-Min RATA 

01/30/2013 13 , 45 

5- 2/~ft. -eM-TOO-£.. 

End of Report , 01/30/2013 17,51 

G12-C4 GI2 -CII G12-C13 

TRACE 

En/'irollmenlai S y stems, In c. 

Validation : All Available Data 

Group#-Channel# GI2 -CIO G12 - C6 G12-C7 G12 - C8 

Long Descrip. 

Short Descrip . 

Units 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2 >Stk 02 2 >NOx Mass 

G12 - C20 

2>StkF!ow 

StkFlow 

kscfh 

0 - 300000 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0 - 1000 

2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk CDc 2>Gas Flow 

G12-C18 

2>NH3 Inj 

NH3Inj 

Ib/hr 

0 -1 000 

G12-C 

2>MW Lo 

MW Lo 

Range 

01/30/ 2 013 13:45 

01/30/2013 13:46 

01/30/2013 13:47 

01/30/2013 13:48 

01/30/2013 13:49 

01/30/2013 13:50 

01/30/2013 13:51 

01/30/2013 13:52 

01/30/2013 13:53 

01/30/2013 13:54 

01/30/2013 13:55 

01/30/2013 13:56 

01/30/2013 13:57 

01/30/2013 13:58 

01/30/2013 13:59 

01/30/2013 1 4 :00 

01/30/2013 14:01 

01/30/2013 14:02 

01/30/2013 14:03 

01/30/2013 14:04 

01/30/2013 14:05 

01/30/2013 14:06 

01/30/2013 14:07 

01/30/2013 14:08 

01/30/2013 14:09 

01/30/2013 1 4 :10 

01/30/2013 14:11 

01/30/ 2 013 14:12 

01/30/ 2 013 14:13 

01/30/ 2 013 14:14 

Date/Time Printed: 

2.8 

44.4 B 

61.0 B 

60.1 B 

21.1 B 

1. 3 B 

6.9 B 

16.1 B 

51.3 B 

57.0 B 

54.5 B 

56.1 B 

56.8 B 

57.0 B 

57.1 B 

57.3 B 

57.1 B 

57.2 B 

57.6 B 

57.4 B 

57.7 B 

57.4 B 

42.7 B 

3.8 B 

2.9 B 

1.1 B 

2.88 

3.2 B 

2.4 B 

2.3 B 

Stk 02 

• 

0- 2 5 

12 . 95 

13 . 2 7 B 

13.34 8 

13.38 B 

14.11 B 

15.878 

15.61 B 

14.54 B 

13.858 

13.808 

13 . 83 B 

13.808 

13. 8 0 B 

13 .8 0 B 

13 . 7 9 B 

13 . 78 B 

13.78 B 

13.77 B 

13.768 

13.76 B 

13 _ 75 8 

13.778 

14.07 B 

15.13 8 

15. 64 B 

15 . 23 B 

14.078 

13. 3 8 B 

13 . 30 B 

13 .3 18 

01/31/2013 12,03 

NOx Mass 

Ib/hr 

0-100 

7.10 

100.00B 

100.00 B 

100.00B 

34.41B 

1.65 B 

10.59 B 

33.04 B 

100.00 B 

100.00B 

100.00B 

100.008 

100.00B 

100.00B 

100.00B 

100.00B 

100.00 B 

100.00 B 

100.00 B 

100.00B 

100.008 

100.00 B 

87.35 B 

5.09 B 

3.85 B 

1 . 66 B 

5.90 B 

7.85 B 

6.19 B 

6.19 B 

20332 

19339 

20090 

19248 

13568 

9923 

13012 

17194 

19835 

20470 

20046 

20483 

20483 

20564 

20459 

20484 

20424 

20492 

20434 

20402 

20422 

20365 

17119 

11462 

11109 

13325 

17470 

21125 

21188 

21199 

3 . 0 

1.58 

0.0 B 

o. a B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

O. a B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.0 B 

0.48 

2.6 B 

4.3 B 

3.9 B 

CO Ma ss 

1b/hr 

0-100 

4 .4 4 

2.43 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0 . 00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0 . 008 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.008 

0.008 

0.008 

0_ 008 

0.008 

0.008 

0. 6 6 B 

4.368 

6.198 

6.19 B 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.126 B 

0.175 B 

0.174 B 

0.068 B 

0.006 B 

0.0288 

0.0558 

0.158 B 

0.174 B 

0.1688 

0.1728 

0.174 B 

0.174 B 

0.175 B 

0.175 B 

0.1748 

0.174 B 

0.175 B 

0 .17 5 B 

0.175 B 

0.175 B 

0.136 B 

0.014 B 

0.012B 

0.0048 

0.0098 

0.0098 

0.007 B 

0.0078 

Stk NOXc 

ppm 

0 - 300 

2.08 

34.33 B 

47.61 B 

47.158 

18.338 

1.528 

7.70 8 

14.948 

42.93 B 

47.378 

45.488 

46.62B 

47 . 20 B 

4 7.37B 

47.388 

47.48 B 

47.32 B 

47.338 

47.60 B 

47.43 B 

47.618 

47.508 

36.89 B 

3.89 B 

3 .2 5 B 

1.14 B 

2.428 

2.51 B 

1.868 

1.798 

Stk CDc Gas hscfh 

p p m 

0-1000 

2.23 

1.16 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0 . 008 

0.00 B 

0 . 00 B 

0 _ 00 8 

0.00 B 

0 . 00 B 

0 . 008 

0.00 B 

0.00 B 

0.00 B 

0.00 B 

0 . 00 B 

0.00 B 

0 . 00 B 

0.00 B 

0.00 B 

0 . 358 

2 . 04 B 

3 . 3 4 B 

3 . 03 B 

hscfh 

0 -1 0000 

8456.4 

7719.6 

7945.8 

7572.6 

4819.8 

2611. 2 

3601.2 

5721.0 

7315.8 

7603.8 

7414.8 

7608.6 

7608.6 

7638.6 

7610.4 

7630.2 

7608.0 

7644.0 

7633.2 

7621. 2 

7639.2 

7596.6 

6117.0 

3460.2 

3057.0 

3952.8 

6242.4 

8311.2 

8424.6 

8418.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1 10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

0-1 

102 

92 . . 

98 

90. 

45. : 

16.: 

32. : 

65 . ! 

89. c 

93. ( 

89 .. 

92 . 

92 . . 

9 2. : 

93. ( 

93 . . 

92. : 

93. 

93.: 

92. : 

93. 

92 . 

66. ( 

25. ! 

22 . . 

36. ( 

71.: 

101.: 

102 

102. ( 

pagE 
Group#-Channel# 

Long Descrip. 

Short Descrip. 

Units 

Range 

01/30/2013 14:15 

01/30/2013 14:16 

01/30/2013 14:17 

01/30/2013 14:18 

01/30/2013 14:19 

01/30/2013 14:20 

01/30/2013 14:21 

01/30/2013 14:22 

01/30/ 20 13 14:23 

01/30/2013 14:24 

01/30/2013 14:25 

01/30/2013 14:26 

01/30/2013 14:27 

01/30/2013 14:28 

01/30/2013 14:29 

01/30/2013 14:30 

01/30/2013 14:31 

01/30/2013 14:32 

01/30/2013 14:33 

01/30/2013 14:34 

01/30/2013 14:35 

01/30/2013 14:36 

01/30/2013 14:37 

01/30/2013 14:38 

01/30/2013 14:39 

01/30/2013 14:40 

01/30/2013 14:41 

01/30/2013 14:42 

01/30/2013 14:43 

01/30/2013 14:44 

01/30/2013 14:45 

01/30/2013 14:46 

01/30/2013 14:47 

01/30/2013 14:48 

01/30/2013 14:49 

01/30/2013 14:50 

01/30/ 2013 14:51 

01/30/ 2013 14:52 

01/30/2013 14:53 

01/30/2013 14:54 

Date/Time Printed: 

G12 - C2 G12-C4 G12 -Cll G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.2 B 

2.2 B 

2.1 B 

2.3 B 

2.2 B 

2.2 B 

2.4 B 

2.4 B 

2.5 B 

2.4 B 

2.5 B 

2.5 B 

2.5 B 

2.5 

2.6 

2.5 

2.6 

2.6 

2.6 

2.7 

2.5 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

Stk 02 

• 

0-25 

13.3 2B 

13.31B 

13.32B 

13.29 B 

13.23 B 

12.96 B 

12.94 B 

12.96 B 

12 .94 B 

12.96 B 

12.96 B 

12.96 B 

12.96 B 

12.95 

12.95 

12. 95 

12.95 

12.94 

12.96 

12.95 

12.97 

12.96 

12 .96 

12.96 

12.97 

12.96 

12.96 

12.95 

12.95 

12.96 

12.95 

12.94 

12.94 

12.95 

12.95 

12.94 

12.95 

12.95 

12.95 

12.95 

01/31/2013 12,03 

NOx Mass 

Ib/hr 

0-100 

5.31 B 

5.31 B 

5.31 B 

6.21 B 

5.31 B 

5.31 B 

6.20 B 

6.19 B 

6.21 B 

6.19 B 

6.19 B 

6.19 B 

6.19 B 

6.20 

6.19 

6.19 

6.19 

6.18 

6.18 

6.16 

6.17 

6.17 

6.17 

6.17 

6.17 

6.17 

6.18 

6.18 

6.18 

6.18 

6.18 

6.19 

6.19 

6.18 

6.18 

6.19 

6.17 

6.19 

6.19 

6.18 

StkFlow 

ksefh 

0-300000 

21235 

21242 

21261 

21234 

20986 

20288 

20251 

20273 

20280 

20282 

20282 

20258 

20284 

20288 

20238 

20261 

20234 

20205 

20232 

20167 

20225 

20210 

20206 

20207 

20224 

20197 

20249 

20228 

20231 

20237 

20231 

20210 

20212 

20218 

20215 

20218 

20197 

20261 

20254 

20215 

G12 - C3 G12-C13 G12-C10 GI2 -C6 G12-C7 G12-C8 G12 -C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW La 

Stk CO 

ppm 

0 - 1000 

3.2 B 

2 . 8 B 

3.0 B 

2.6 B 

2.4 B 

2.6 B 

2.4 B 

2.2 B 

2.3 B 

2.2 B 

2.1 B 

1. 9 B 

1. 9 B 

2.0 

1.9 

1.9 

2.0 

1.9 

1.9 

1.8 

1.8 

1.6 

1.6 

1.7 

1.7 

1.5 

1.6 

1.5 

1.6 

1.4 

1.5 

1.5 

1.5 

1.6 

1.7 

1.7 

1.5 

1.7 

1.5 

1.4 

CO Mass 

Ib/hr 

• 0-100 

5.31 B 

4.43 B 

4.43 B 

4.44 B 

3.54 B 

3.54 B 

3.54 B 

3.54 B 

3.55 B 

3.54 B 

2.65 B 

2.65 B 

2.65 B 

2.66 

2.65 

2 . 65 

2.65 

2.65 

2.65 

2.64 

2.64 

2.64 

2.64 

2.64 

2.64 

1. 76 

2.65 

1. 77 

2.65 

1. 77 

1. 77 

1. 77 

1. 77 

2.65 

2.65 

2.65 

1. 76 

2.65 

1. 77 

1. 77 

NOx Rate 

Ib/mmBtu 

0-1 

0.006 B 

0.006 B 

0.006 B 

0.007 B 

0.006 B 

0.0068 

0.007 B 

0.00 7 B 

0 .0 078 

0.007 B 

0.007 B 

0.007 B 

0.007 B 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1.71 B 

1. 71 B 

1.63 B 

1. 78 B 

1.69 B 

1. 63 B 

1.78 B 

1.78 B 

1.85 B 

1.78 B 

1.86 B 

1. 86 B 

1.86 B 

1. 86 

1.93 

1. 86 

1. 93 

1. 93 

1. 93 

2.00 

1. 86 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

1. 93 

2.00 

2.00 

1. 93 

2.00 

2.00 

2.00 

Stk COe Gas 

ppm 

0-1000 

hscfh 

hsefh 

0-10000 

2.4 9 B 

2.18 B 

2.34 B 

2.02 B 

1.85 B 

1.93 B 

1. 78 B 

1. 63 B 

1.70 B 

1.63 B 

1.56 B 

1.41 B 

1.41 B 

1. 48 

1.41 

1.41 

1. 48 

1.41 

1.41 

1.34 

1.34 

1.19 

1.19 

1.26 

1. 26 

1.11 

1.19 

1.11 

1.19 

1. 04 

1.11 

1.11 

1.11 

1.19 

1.26 

1.26 

1.11 

1.26 

1.11 

1. 04 

8421.0 

8434.8 

8431.2 

8454.0 

8421.0 

8427.6 

8433.6 

8421. 6 

8445.6 

8425.2 

8425.2 

8415.0 

8425.8 

8438.4 

8417.4 

8427.0 

8415.6 

8414.4 

8404.2 

8388.0 

8391.0 

8395.2 

8393.4 

8394.0 

8390.4 

8389.8 

8411. 4 

8413.2 

8414.4 

8406.6 

8414.4 

8416.2 

8417.4 

8409.0 

8407.8 

8419.8 

8400.6 

8427.0 

8424.0 

8407.8 

NIB Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1 10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

MW La 

0-1 

102 .. 

102 .. 

102. 

102 

102.1 

102. : 

102 . 

102 .. 

102 . 

102 .. 

102. : 

102. ~ 

102 .. 

103. : 

102 ' 

102 .. 

102 . : 

102. : 

102.: 

101. : 

102.: 

102.1 

102. : 

101. : 

101. . 

102. 1 

102.: 

102.: 

102.: 

102 . ! 

102. ! 

102. : 

102. : 

102 . . 

102. 

102.1 

102.1 

102 

102 .. 

102. ~ 

Pag~ 
Group#-Channel# 

Long Descrip. 

Short Descri p . 

Un its 

Range 

01/30/2013 14:55 

01/30/2013 14:56 

01/30/2013 14:57 

01/30/2013 14:5S 

01/30/2013 14:59 

01/30/2013 15:00 

01/30/2013 15:01 

01/30/2013 15:02 

01/30/2013 15:03 

01/30/2013 15:04 

01/30/2013 15:05 

01/30/2013 15:06 

01/30/2013 15:07 

01/30/2013 15:0S 

01/30/2013 15:09 

01/30/2013 15:10 

01/30/2013 15:11 

01/30/2013 15:12 

01/30/2013 15:13 

01/30/2013 15:14 

01/30/2013 15:15 

01/30/2013 15:16 

01/30/2013 15:17 

01/30/2013 15:18 

01/30/2013 15:19 

01/30/2013 15:20 

01/30/2013 15:21 

01/30/2013 15:22 

01/30/2013 15:23 

01/30/2013 15:24 

01/30/2013 15:25 

01/30/2013 15:26 

01/30/2013 15:27 

01/30/2013 15:28 

01/30/2013 15:29 

01/30/2013 15:30 

01/30/2013 15:31 

01/30/2013 15:32 

01/30/2013 15:33 

01/30/2013 15:34 

Date/Time Printed: 

G12-C2 G12-C4 G12 -Cll 

2>stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.8 

2.7 

2.7 

2.7 

2.7 

2.8 

2.8 

2.7 

Stk 02 

• 

0-25 

12.96 

12.94 

12.95 

12.95 

12.96 

12.96 

12.95 

12.95 

12.95 

12.95 

12.95 

12.96 

12 . 96 

12.97 

12.96 

12.96 

12 . 96 

12.96 

12.96 

12.95 

12.96 

12.94 

12.94 

12.95 

12.95 

12.95 

12.95 

12.95 

12.95 

12.95 

12.94 

12.96 

12.93 

12.93 

12.92 

12.93 

12.93 

12 . 91 

12.92 

12.92 

01/31/2013 12,03 

NOx Mass 

Ib/hr 

0 -100 

6.18 

6.1S 

6.1S 

6.18 

6.16 

6.17 

6.17 

6.17 

6.17 

6.18 

6.18 

6.16 

6.17 

6.16 

6.17 

6.17 

6.16 

6.1S 

6.17 

6.1S 

6.16 

6.18 

6.19 

6.17 

6.1S 

6.17 

6.1S 

6.18 

6.18 

6.18 

6.19 

6.1S 

7.0S 

6.20 

6.20 

6.20 

6.20 

7.10 

7.10 

6.21 

G12-C20 

2>StkFlow 

StkFlow 

ksefh 

0-300000 

20243 

20201 

20222 

2020) 

20167 

20197 

20180 

20186 

20189 

20225 

20205 

20174 

20204 

20204 

20200 

20220 

20182 

20236 

20197 

20203 

20190 

20175 

2 0208 

20172 

20203 

20184 

20213 

20231 

20202 

20222 

2 0223 

20239 

20216 

20230 

20215 

20220 

20227 

20214 

20235 

20225 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

1.6 

1.5 

1.6 

1.6 

1.5 

1.5 

1.6 

1., 

1.5 

1., 

1.' 

1., 

1.5 

1., 

1.3 

1.5 

1.3 

1.4 

1.5 

1.4 

1.6 

1.3 

1.4 

1.3 

1.4 

1.3 

1.3 

1.5 

1.3 

1.5 

1.4 

1.7 

1.5 

1.5 

1.5 

1.7 

1.7 

2.0 

1.6 

1.9 

G12-Cl3 G12 -C10 G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXe 

CO Mass 

Ib/hr 

0-100 

2.65 

1. 77 

2.65 

2.65 

1. 76 

1. 76 

2.64 

1. 76 

1. 76 

1. 77 

1. 76 

1. 76 

1. 76 

1. 76 

1. 76 

1. 76 

1. 76 

1. 77 

1. 76 

1. 76 

2.64 

1. 76 

1. 77 

1. 76 

1. 76 

1. 76 

1. 77 

1. 77 

1. 76 

1. 77 

1.77 

2.65 

1.77 

1. 77 

1. 77 

2.66 

2.66 

2.66 

2.66 

2.66 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

stk NOXc 

ppm 

0-300 

1. 93 

2.00 

2.00 

2.00 

1. 93 

2.01 

1. 93 

2.00 

1. 93 

2.00 

2.00 

1. 93 

2.01 

2.01 

2.01 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

2.00 

2.00 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

2.07 

2.00 

2.00 

2.00 

2.00 

2.07 

2.07 

2.00 

G12-C7 G12 - CS 

2>Stk COe 2>Gas Flow 

Stk COc Gas hscfh 

ppm hsefh 

0-1000 0-10000 

1.19 

1.11 

1.19 

1.19 

1.11 

1.11 

1.19 

1. 04 

1.11 

1. 04 

1. 04 

1. 04 

1.11 

1. 04 

0. 9 7 

1.11 

0.97 

1. 04 

1.11 

1.04 

1.19 

0.96 

1. 04 

0.96 

1. 04 

0.96 

0.96 

1.11 

0.96 

1.11 

1. 04 

1.26 

1.11 

1.11 

1.11 

1. 26 

1. 26 

1. 4 S 

1.18 

1. 40 

8409.0 

8412.6 

S410.8 

8403.0 

8377.2 

8389.8 

8393.4 

8395.8 

8397.0 

8412.0 

8403.6 

8380.2 

8392.8 

8382.0 

8391. a 

8399.4 

8383.8 

8406. a 

8389.8 

8403.0 

8386.8 

8401.8 

8415.6 

8389.8 

8403.0 

8395.2 

8407.2 

8414.4 

8402.4 

8410.8 

8421.6 

8407.2 

8429.4 

8435.4 

8439.6 

S431. 2 

8434.2 

8449.8 

8448.0 

8443.8 

G12-C1S 

2>NH3 Inj 

NH3Inj 

1b/br 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110. a 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

102 . ~ 

102 .. 

102. 

102. 

102 . . 

102. : 

102 .. 

102. ( 

102. ! 

102. ! 

102. : 

101. . 

102.c 

101.1 

102 . . 

102. : 

102. c 

102. ! 

102. ~ 

102 . . 

102. c 

102. ! 

102. : 

102. : 

102. ! 

102.! 

102 . . 

102. 

102.: 

102.: 

102 . ! 

102.! 

103.: 

102. : 

102 

102 

102.: 

102.: 

103.' 

103.! 

pagE 
Group#-Channel# 

Long Descrip . 

Short Descrip . 

Uni ts 

Range 

01/30/2013 15:35 

01/30/2013 15:36 

01/30/2013 15:37 

01/30/2013 15:38 

01/30/2013 15:39 

01/30/2013 15 : 40 

01/30/2013 15:41 

01/30/2013 15:42 

01/30/2013 15:43 

01/30/2013 15:44 

01/30/2013 15:45 

01/30/2013 15:46 

01/30/2013 15:47 

01/30/2013 15:48 

01/30/2013 15:49 

01/30/2013 15:50 

01/30/2013 15:51 

01/30/2013 15:52 

01/30/2013 15:53 

01/30/2013 15:54 

01/30/2013 15:55 

01/30/2013 15:56 

01/30/2013 15:57 

01/30/2013 15:58 

01/30/2013 15:59 

01/30/2013 16:00 

01/30/2013 16:01 

01/30/2013 16:02 

01/30/2013 16:03 

01/30/2013 16:04 

01/30/2013 16 : 05 

01/30/2013 16:06 

01/30/2013 16:07 

01/30/2013 16;08 

01/30/2013 16:09 

01/30/2013 16;10 

01/30/2013 16;11 

01/30/2013 16;12 

01/30/2013 16;13 

01/30/2013 16:14 

Date/Time Printed: 

G12 -C2 G12-C4 G12 - CII 

2:>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2:>Stk 02 2:>NOx Mass 

2.7 

2.8 

2.7 

2.8 

2.7 

2.7 

2.8 

2.7 

2.8 

2.8 

2.7 

2.9 

2.8 

2.8 

2.8 

2.8 

2 . 7 

2.8 

2.8 

2.8 

2.7 

2.8 

2.8 

2.8 

2.7 

2.7 

2.7 

2.7 

2 .7 

2.7 

2.7 

2 . 7 

2.7 

2.8 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

Stk 02 

• 

0-25 

12.91 

12.91 

12.92 

12.91 

12.91 

12 . 91 

12.89 

12.90 

12.90 

12.90 

12.91 

12.89 

12.89 

12 . 88 

12.89 

12.89 

12.92 

12.91 

12.91 

12.91 

12.93 

12.92 

12.91 

12.92 

12.93 

12.92 

12.93 

12.93 

12.93 

12.94 

12.93 

12 . 93 

12.93 

12.93 

12.93 

12.94 

12 . 94 

12.92 

12.93 

12.93 

01(31(2013 12 , 03 

NOx Mass 

lb/hr 

0-100 

6.21 

7.12 

6.22 

7 . 12 

6 . 23 

6 . 22 

7.14 

6.24 

7.14 

7.13 

6.23 

7.13 

7.14 

7.16 

7.14 

7.15 

6 . 22 

7.11 

7.12 

7.12 

6.21 

7.10 

7.11 

7.11 

6.20 

6.20 

6.19 

6.18 

6.20 

6.18 

6.20 

6.19 

6.21 

7.09 

6 . 19 

6.18 

6.20 

6.21 

6.20 

6.20 

G12-C20 

2:>StkFlow 

StkFlow 

ksefh 

0-300000 

20227 

20264 

20254 

20271 

20279 

20257 

20281 

20296 

20305 

20276 

20293 

20262 

20274 

20323 

20274 

20305 

20255 

20260 

20287 

20290 

20259 

20255 

20257 

20271 

20239 

20215 

20197 

20176 

20220 

20182 

20243 

20212 

20262 

20236 

20203 

20202 

20261 

20239 

20227 

20216 

G12 - C3 

2:>Stk CO 

Stk CO 

ppm 

0-1000 

1.7 

1.8 

1.5 

1.3 

1.7 

1.5 

1.9 

1.9 

2 . 1 

2.3 

2 . 4 

2.4 

2.2 

2.4 

2.2 

2.2 

2.3 

2.4 

2.4 

2.4 

2.4 

2.7 

2.8 

2.5 

2.7 

2.7 

2.9 

2.8 

2.7 

2.7 

2.6 

2.8 

2.7 

2.8 

2.7 

2.8 

2.9 

2.8 

2.9 

2.9 

GI2 - CD G12-CIO Gl2 -C6 

2:>CO Mass 2:>NOx Rate 2:>Stk NOXe 

CO Mass 

1b(hr 

0-100 

2 . 66 

2.67 

1. 78 

1. 78 

2.67 

1. 78 

2.68 

2.68 

2 . 68 

3 . 56 

3.56 

3.57 

3.57 

3.58 

3 . 57 

3.57 

3.55 

3.56 

3.56 

3.56 

3.55 

3.55 

4.45 

3.55 

3.54 

3.54 

4.42 

4.42 

3 . 54 

3.53 

3.55 

4.42 

3.55 

4.43 

3.54 

4.42 

4.43 

4 . 44 

4.43 

4.43 

NOx Rate 

lb/mmBtu 

0~1 

0.007 

0.008 

0.007 

0.008 

0.007 

0.007 

0.008 

0.007 

0.008 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0.007 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0 . 008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.008 

0.007 

0 . 007 

0 . 007 

0 . 007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1. 99 

2.07 

2.00 

2.07 

1. 99 

1. 99 

2.06 

1. 99 

2.07 

2.07 

1. 99 

2.14 

2.06 

2.06 

2.06 

2.06 

2.00 

2.07 

2.07 

2.07 

2.00 

2.07 

2.07 

2.07 

2.00 

2. 00 

2.00 

2 . 00 

2.00 

2.00 

2 . 00 

2.00 

2 . 00 

2 . 07 

2.00 

2.00 

2.00 

2 . 00 

2.00 

2.00 

G12 -C7 G12 -C8 

2:>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hscfh 

0 - 1000 

1. 26 

1. 33 

1.11 

0.96 

1. 26 

1.11 

1. 40 

1. 40 

1. 55 

1. 70 

1. 77 

1. 77 

1. 62 

1. 77 

1. 62 

1. 62 

1. 70 

1. 77 

1. 77 

1. 77 

1. 78 

2.00 

2 . 07 

1. 85 

2.00 

2.00 

2 . 15 

2.07 

2 . 00 

2.00 

1. 92 

2.07 

2 . 00 

2 . 07 

2.00 

2.08 

2.15 

2 . 07 

2.15 

2.15 

0 - 10000 

8 4 55.2 

8470.8 

8455.8 

8473.8 

8476.8 

8467 . 8 

8499.0 

8494.8 

8498 . 4 

8486.4 

8482 . 8 

8491 2 

8496.0 

8527 . 2 

8496 . 0 

8509 . 2 

8456.4 

8469 . 0 

8480 . 4 

8481.6 

8447.4 

8456.4 

8467.8 

8463.0 

8439.0 

8439.6 

8421.6 

8412.6 

8431.2 

8404.8 

8440.8 

8427.6 

8448 . 6 

8437 . 8 

8424.0 

8413.2 

8437 . 8 

8449 . 8 

8434 . 2 

8429.4 

G12-C18 

2>NH3 Inj 

NH3Inj 

1b(hr 

0-1000 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110 . 0 

110 . 0 

110 . 0 

110 . 0 

110.0 

110 . 0 

110 . 0 

110 . 0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110 . 0 

2:>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

~1 

103.1 

103 .. 

103. : 

103. : 

103. : 

103. : 

103 

103 . : 

103 . . 

103. ! 

103 .. 

104 . ( 

104 . 1 

104. ' 

103. : 

104.: 

103,1 

103. : 

103. ! 

103 .. 

102. : 

103.: 

103. ! 

103.1 

103, : 

103. ( 

102. ' 

102. ( 

102. : 

102 .. 

102. ! 

102. ; 

102. ! 

102 .. 

102. 

102, . 

102 . 

103. I 

102 .. 

103. I 

pag( 
Group#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

01/30/2013 16:15 

01/30/2013 16:16 

01/30/2013 16:17 

01/30/2013 16:18 

01/30/2013 16:19 

01/30/2013 16:20 

01/30/2013 16:21 

01/30/2013 16 : 22 

01/30/2013 16:23 

01/30/2013 16:24 

01/30/2013 16:25 

01/30/2013 16:26 

01/30/2013 16:27 

01/30/2013 16:28 

01/30/2013 16:29 

01/30/2013 16:30 

01/30/2013 16:31 

01/30/2013 16:32 

01/30/2013 16:33 

01/30/2013 16:34 

01/30/2013 16:35 

01/30/2013 16:36 

01/30/2013 16:37 

01/30/2013 16:38 

01/30/2013 16:39 

01/30/2013 16:40 

01/30/2013 16:41 

01/30/2013 16:42 

01/30/2013 16:43 

01/30/2013 16:44 

01/30/2013 16:45 

01/30/2013 16:46 

01/30/2013 16:47 

01/30/2013 16:48 

01/30/2013 16:49 

01/30/2013 16:50 

01/30/2013 16:51 

01/30/2013 16 : 52 

01/30/2013 16:53 

01/30/2013 16:54 

Date/Time Printed: 

G12-C2 G12 - C4 G12 - C1 1 G12-C20 

2>Stk NOx 

Stk NOx 

2>Stk 02 2>NOx Mass 2>StkFlow 

ppm 

0-150 

2.7 

2.7 

2.8 

2.6 

2.7 

2.8 

2.7 

2.8 

2.7 

2.7 

2.7 

2.7 

2 . 7 

2.7 

2.7 

2.8 

2.7 

2.6 

2.6 

2.6 

2.7 

2.7 

2.7 

2 . 7 

2.7 

2.7 

2.8 

2.7 

2.8 

2.B 

2.B 

2.7 

2.8 

2.7 

2.7 

2.7 

2.6 

2.6 

2.7 

2.6 

Stk 02 

• 

0-25 

12.91 

12.92 

12 . 91 

12.94 

12.94 

12.93 

12.93 

12.93 

12.94 

12.94 

12.93 

12.93 

12.93 

12 . 93 

12 . 92 

12 .91 

12.93 

12.93 

12.93 

12.94 

12.94 

1 2 .93 

12.94 

12.94 

12.93 

12.92 

12.91 

12 . 91 

12.91 

12.90 

12.90 

12.91 

12.90 

12 . 92 

12.93 

12.93 

12.95 

12.94 

12.94 

12.96 

01/31/2013 12,03 

NOx Mass 

1b/hr 

0 - 100 

6.21 

6.21 

7.11 

6.18 

6.18 

7.09 

6.20 

7 . 09 

6 . 19 

6 . 19 

6 . 20 

6.21 

6.19 

6.20 

6.21 

7.10 

6.20 

6.20 

6.20 

6.19 

6 . 20 

6.21 

6.19 

6.21 

6.20 

6.23 

7.11 

6 . 23 

7.13 

7.14 

7.13 

6.22 

7.12 

6.23 

6.22 

6 .2 2 

6.20 

6.21 

6.21 

6.19 

StkFlow 

ksefh 

0-300000 

20205 

20239 

20243 

20182 

20191 

20252 

20219 

20233 

20210 

20237 

20240 

20252 

20206 

20243 

20249 

20221 

20226 

20213 

20216 

20218 

20248 

20260 

20224 

20277 

20236 

20291 

20260 

20293 

20310 

20305 

20272 

20251 

20243 

20303 

20301 

20308 

20287 

20276 

20277 

20260 

G12-C3 G12-C13 G12-C10 G12-C6 G12 - C7 Gl2-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

2.8 

2.9 

2.8 

2.9 

3.0 

3.0 

3.0 

2.9 

2.9 

2.9 

3.0 

3.1 

3.1 

3.1 

3.2 

3.1 

3.2 

3.3 

3.3 

3.2 

3.4 

3.2 

3.1 

3.2 

3.2 

3.2 

3.1 

3.2 

3.1 

3.3 

2.9 

3.1 

3.0 

3.1 

3 . 1 

3.2 

3.3 

3.3 

3.1 

3 . 4 

CO Mass 

lb/hr 

0-100 

4.43 

4.44 

4.44 

4.41 

4 . 41 

4.43 

4.43 

4.43 

4.42 

4.42 

4.43 

4.43 

4.42 

4 . 43 

4.44 

4.44 

4.43 

4.43 

4.43 

4.42 

5.31 

4.44 

4 . 42 

4.43 

4.43 

4.45 

4.45 

4.45 

4.46 

4.46 

4.45 

4.44 

4.45 

4.45 

4.44 

4.45 

4.43 

4.43 

4 . 43 

5.30 

NOx Rate 

lb/mmBtu 

0-1 

0 . 007 

0.007 

0.008 

0.007 

0.007 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0 . 007 

0 . 007 

0.007 

0.007 

0.008 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0 . 007 

0 . 008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXe 

ppm 

0-300 

1. 99 

2.00 

2.07 

1. 93 

2.00 

2.07 

2.00 

2.07 

2.00 

2.00 

2 . 00 

2 . 00 

2.00 

2.00 

2.00 

2.07 

2.00 

1. 92 

1. 92 

1. 93 

2.00 

2 . 00 

2.00 

2.00 

2.00 

2.00 

2.07 

1. 99 

2.07 

2.07 

2.07 

1. 99 

2 . 07 

2.00 

2.00 

2.00 

1. 93 

1. 93 

2.00 

1. 93 

Stk COe Gas hsefh 

ppm hscfh 

0 - 1000 0 - 10000 

2.07 8446.2 

2.14 8449.8 

2.07 8461.8 

2.15 8404 . 8 

2.22 8408.4 

2.22 8444 . 4 

2.22 8430 . 6 

2.15 8436.6 

2.15 8416.2 

2.15 8427.6 

2.22 8439.6 

2.29 8444 . 4 

2.29 8425 . 2 

2.29 8440 . 8 

2.37 8454.0 

2.29 8452.8 

2.37 8433.6 

2.44 8428.2 

2.44 8429.4 

2.37 8419.8 

2.52 8432.4 

2.37 8448.0 

2.30 8422.2 

2.37 8444.4 

2.37 8437.8 

2.37 8471.4 

2.29 8469.0 

2.36 8482.8 

2.29 8490.0 

2.43 8498.4 

2.14 8484 . 6 

2.29 8465.4 

2.21 8472.6 

2.29 8476.2 

2.29 8464.8 

2.37 8467.8 

2.45 8437.8 

2.45 8443.8 

2.30 8444.4 

2.53 84 1 6 . 2 

NH3Inj 

Ib/hr 

0 - 1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1 10.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I - Min RATA - Continued 

MW Lo 

0-1 

102 . 

103.1 

103. ( 

101. . 

102. ! 

103.1 

102 .. 

102 .. 

102.1 

102.: 

103.: 

102 .. 

102. : 

103 

102 . 

102. : 

102. 

102. 

102 . . 

102.: 

102. 

102. ! 

102 . . 

102 . . 

102 . . 

103. : 

103 . : 

103.1 

103. ! 

1 03. : 

103. 1 

103. ( 

103.( 

103. 1 

102 .. 

102. 

102. : 

102 .. 

102 .. 

102.1 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descri p . 

Units 

Range 

01/30/2013 16:55 

01/30/2013 16:56 

01/30/2013 16:57 

01/30/2013 16:58 

01/30/2013 16:59 

01/30/2013 17:00 

01/30/2013 17:01 

01/30/2013 17:02 

01/30/2013 17:03 

01/30/2013 17:04 

01/30/2013 17:05 

01/30/2013 17:06 

01/30/2013 17:07 

01/30/2013 17:08 

01/30/2013 17:09 

01/30/2013 17:10 

01/30/2013 17:11 

01/30/2013 17:12 

01/30/2013 17:13 

01/30/2013 17:14 

01/30/2013 17;15 

01/30/2013 17:16 

01/30/2013 17;17 

01/30/2013 17:18 

01/30/2013 17:19 

01/30/2013 17:20 

01/30/2013 17:21 

01/30/2013 17:22 

01/30/2013 17:23 

01/30/2013 17:24 

01/30/2013 17:25 

01/30/2013 17:26 

01/30/2013 17;27 

01/30/2013 17:28 

01/30/2013 17:29 

01/30/2013 17:30 

01/30/2013 17:31 

01/30/2013 17:32 

01/30/2013 17:33 

01/30/2013 17:34 

Date/Time Printed: 

G12 -C2 G12 -C4 G12 -C11 G12 - C20 

2;:.Stk NOx 

Stk NOx 

ppm 

0 - 150 

2~Stk 02 2~NOx Mass 2;:.StkFlow 

2.7 

2.6 

2.7 

2.6 

2.6 

2.6 

2.7 

2.7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.8 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2 . 7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.8 

2.7 

2.7 

Stk 02 

• 

0-25 

12.95 

12.97 

12.96 

12.97 

12.96 

12.95 

12.94 

12 . 93 

12.93 

12.93 

12.93 

12.92 

12.93 

12 . 92 

12.93 

12.91 

12.92 

12.92 

12.93 

12.93 

12 . 93 

12.92 

12.92 

12 . 92 

12.93 

12.93 

12.91 

12.93 

12.92 

12.94 

12.93 

12.93 

12.93 

12.93 

12.93 

12 . 9 2 

12.91 

1 2 .91 

12.91 

12.92 

01/31/2013 12,03 

NOx Mass 

Ib/hr 

0-100 

6.18 

6.16 

6.16 

6.16 

6.16 

6.18 

6.20 

6.21 

6.21 

6.21 

6.23 

6.24 

6.23 

7.13 

6.23 

6.25 

6.25 

6.24 

6.24 

6.22 

6.23 

6.24 

6.23 

6.25 

6.23 

6.24 

6.25 

6.25 

6.24 

6.23 

6.23 

6.23 

6.23 

6.23 

6.24 

6.25 

6.25 

7.16 

6.24 

6.24 

StkFlow 

kscfh 

0-300000 

20215 

20189 

20174 

20195 

20184 

20208 

20238 

20255 

20255 

20255 

20321 

20323 

20334 

20321 

20340 

20342 

20353 

20343 

20345 

20291 

20322 

20340 

20316 

20362 

20325 

20377 

20336 

20383 

20347 

20351 

20318 

20325 

20322 

20314 

20358 

20367 

20339 

20378 

20317 

20340 

G12-C3 G12 -CD G12-C10 G12-C6 G12-C7 G12 - C8 G12-C18 G12-C 

2;:.Stk CO 2;:.CO Mass 2;:.NOx Rate 2;:.Stk NOXc 2~Stk COc 2;:.Gas Flow 2;:.NH3 Inj 2;:.MW La 

Stk CO 

ppm 

0-1000 

3.4 

3.4 

3.9 

3.7 

3.6 

3.7 

3.6 

3.3 

3.3 

3.3 

3.5 

3.4 

3.6 

3.3 

3.6 

3.5 

3.6 

3.6 

3.6 

3.8 

3.9 

3.7 

3.8 

3.8 

3.6 

3.8 

3.6 

3.8 

3.6 

3.7 

3.7 

3.6 

3.7 

3.6 

4.0 

3.8 

3.8 

3.4 

3.8 

3.6 

CO Mass 

lb/hr 

0-100 

5.30 

5.28 

5.28 

5.28 

5.28 

5.30 

5.31 

4.43 

4.43 

4.43 

5.34 

5.35 

5.34 

4.45 

5.34 

5.36 

5.35 

5.35 

5.34 

5.33 

5.34 

5.35 

5.34 

5.36 

5.34 

5 . 35 

5.36 

5 . 35 

5.35 

5.34 

5.34 

5.34 

5.34 

5.34 

6.24 

5.36 

5.36 

5.37 

5.35 

5.35 

NOx Rate 

lb/mmBtu 

0 - 1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

Stk NOXc 

ppm 

0 - 300 

2.00 

1. 93 

2.01 

1. 93 

1. 93 

1. 93 

2.00 

2.00 

2.00 

2.00 

1. 92 

2.00 

2.00 

2.07 

2.00 

1. 99 

1. 92 

2.00 

1. 92 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

1. 99 

2.00 

1. 92 

2.00 

2.00 

1. 92 

2.00 

2.00 

1. 92 

2.00 

1. 99 

2.07 

1. 99 

2.00 

Stk COc Gas 

ppm 

hscfh 

hscfh 

0-1000 

2.52 

2.53 

2.90 

2.75 

2.68 

2.75 

2.67 

2 .44 

2.44 

2.44 

2.59 

2.51 

2 . 66 

2.44 

2.66 

2.58 

2.66 

2.66 

2.66 

2.81 

2.89 

2,.74 

2.81 

2.81 

2 . 66 

2.81 

2.66 

2.81 

2.66 

2.74 

2.74 

2.66 

2.74 

2.66 

2.96 

2.81 

2.81 

2 . 51 

2.81 

2.66 

0-10000 

8407.8 

8376.0 

8380.2 

8378.4 

8384.4 

8404.8 

8428.2 

8445.6 

8445.6 

8445.6 

8473.2 

8484.6 

8478.6 

8484.0 

8481.0 

8503.2 

8497.2 

8493.0 

8483.4 

8460.6 

8473.8 

8491. 8 

8481.6 

8500.8 

8475.0 

8496.6 

8500.8 

8499.0 

8494.8 

8475.0 

8472.0 

8475.0 

8473.8 

8470.2 

8488.8 

8503.2 

8502.0 

8518.2 

8493.0 

8491 . 8 

NH3Inj 

1b/hr 

0-1000 

110.0 

llO .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

MW La 

0-1 

102. : 

101. ! 

101. 

101. 

102.1 

102 . : 

102.: 

103 . ! 

103.J 

10) .J 

103.J 

103. ! 

103. : 

104.1 

102. 

103.: 

103 . ~ 

103. ! 

103.: 

102. : 

103.: 

103.1 

103.1 

103. : 

103. ! 

103.: 

103. ! 

103 

103. 

103.1 

102. 

102. 

103.1 

103.: 

103 .. 

103.! 

103.! 

103. : 

103 .. 

103 . . 

Pagf 
Group #-Channel# 

Long Descrip . 

Short Descrip . 

Units 

Range 

01/30/2013 17:35 

01/30/2013 17:36 

01/30/2013 17:37 

01/30/2013 17:38 

01/30/2013 17:39 

01/30/2013 17:40 

01/30/2013 17:41 

01/30/2013 17:42 

01/30/ 2 013 17:43 

01/30/2013 17:44 

01/30/2013 17:45 

01/30/2013 17:46 

01/30/2013 17:47 

01/30/2013 17:48 

01/30/2013 17:49 

01/30i2 013 17:50 

01/30/2013 17:51 

Period Average 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2.8 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.8 

2.7 

2.7 

2.6 

2.6 

2.6 

2.7 

2.6 

6.7 

61. 0 

1.1 

G12-C4 G12-C11 G12-C20 

2>Stk 02 2>NOx Mass 2>StkFlow 

Stk 02 

% 

0-25 

12 . 91 

12.93 

12.93 

12.92 

12.92 

12.92 

1 2.91 

12.91 

12.92 

12.92 

12.91 

12.91 

12.93 

12 .93 

12.94 

12.94 

12 . 96 

13.07 

15.87 

12.88 

NOx Mass 

lb/hr 

0-100 

7.15 

6.24 

6.25 

6.26 

6.26 

6.27 

6.28 

6.27 

6.26 

7.15 

6.27 

6.25 

6.24 

6.23 

6.23 

6.23 

6.20 

13 .29 

100.00 

1. 65 

StkFlow 

kscfh 

0-300000 

20356 

20361 

20393 

20400 

20405 

20428 

2 0429 

20424 

20409 

20379 

20401 

20339 

20367 

2 0317 

20342 

20346 

20323 

20054 

21261 

9923 

G12-C3 G12-C13 GI2-CI0 G12-C6 G12 - C7 G12-CS G12 -CIS G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

3.7 

3.7 

3.9 

3.7 

3.7 

3.8 

3.6 

4.0 

3.7 

4.0 

3.8 

3.8 

3.7 

3 . 9 

3.9 

3.8 

4.0 

2.4 

4.3 

0.0 

CO Mass 

lb/hr 

0-100 

5.36 

5.35 

5.36 

5.37 

5.37 

5.37 

5.38 

6.27 

5.37 

6.25 

5.37 

5.36 

5.35 

5.34 

5.34 

5.34 

6.20 

3.40 

6.27 

0.00 

NOx Rate 

lb/mmBtu 

0-1 

0.008 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0 .0 0 7 

0.007 

0.019 

0.175 

0.004 

Stk NOXc 

ppm 

0-300 

2.07 

2.00 

2.00 

2.00 

2.00 

2.00 

1. 99 

1. 99 

2.00 

2.07 

1. 99 

1. 99 

1. 92 

1. 92 

1. 93 

2.00 

1. 93 

5.31 

47.61 

1.14 

Stk CDc Gas 

ppm 

0-1000 

hscfh 

hsefh 

0-10000 

2.73 

2 . 74 

2.S9 

2.74 

2.74 

2.S1 

2 .66 

2.95 

2. 74 

2.96 

2.81 

2.81 

2.74 

2.89 

2.89 

2.82 

2.97 

1. 75 

3.34· 

0.00 

8509.2 

8490.0 

8503.2 

8517.0 

8518.8 

8528.4 

8539.8 

8537.4 

8520.6 

8508.0 

8527.8 

8502.0 

8492.4 

8471 4 

8471.4 

8473.2 

8442.0 

8239.1 

8539.8 

2611.2 

NH3Inj 

lb/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

MW Lo 

0-1 

103 

103. 

104.1 

103. 

104. ! 

104. : 

10 4 . 

103 .. 

104. ! 

103. ! 

103 .. 

103 .. 

103. 

103 . . 

102 .. 

103.1 

102. : 

99.8 

104. 

16. 

1. 6448E+3 3.2285E+3 3.2827E+3 4.9533E+6 5.8170E+2 8.3991E+2 4.8029E+0 1.3127E+3 4.3164E+2 2.0350E+6 2.7170E+4 2.4671E+ 

100.0 100 . 0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100.0 100. 

01/31/2013 12,03 2>Summary - l-Min RATA - Continued Pag{ 
Data Summary Report 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 

Source : Turbine 2 

Data Group: 2>1~Min Cales 

Report Name: 

CPJ ')~, Ul\~t 2-

~ \ 3~~ - I'':)' \(A't-, b ~A4 TRACE 

92240 

5- Z/trr'l- _~fA.- 100-1 

Ellvironmellta l S ystems, Illc. 

Start of Report : 

2>Summary - I-Min RATA 

01/30/2013 13,45 End of Report: 01/30/2013 17:51 validation: Valid Data Only 

Group#-Channel# 

Lo ng Descrip . 

Short Descrip . 

Units 

Range 

01/30/2013 13:45 

01/30/2013 13:46 

01/30/2013 13:47 

01/30/2013 13:48 

01/30/ 2 013 13:49 

01/30/2013 13:50 

01/30/2013 13:51 

01/30/2013 13:52 

01/30/2013 13:53 

01/30/2013 13:54 

01/30/2013 13:55 

01/30/2013 13:56 

01/30/2013 13:57 

01/30/2013 13:58 

01/30/2013 13:59 

01/30/2013 14:00 

01/30/2013 14:01 

01/30/2013 14:02 

01/30/2013 14:03 

01/30/2013 14:04 

01/30/ 2 013 14:05 

01/30/2013 14:06 

01/30/2013 14:07 

01/30/2013 14:08 

01/30/2013 14:09 

01/30/2013 14:10 

01/30/2013 14:11 

01/30/2013 14:12 

01/30/2013 14:13 

01/30/2013 14:14 

Date/Time Printed: 

G12-C2 G12-C4 G12-Cll 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.8 

Stk 02 

% 

0-25 

12.95 

01/31/2013 12,03 

NOx Mass 

1b/hr 

0-100 

7.10 

GI2 -C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20332 

19339 

20090 

19248 

13568 

992 3 

13012 

17194 

19835 

20470 

20046 

20483 

20483 

20564 

20459 

20484 

20424 

20492 

20434 

20402 

20422 

20365 

17119 

11462 

11109 

13325 

17470 

21125 

21188 

21199 

GI2-C) 

2>Stk CO 

Stk CO 

ppm 

0-1000 

3.0 

GI2-Cl3 GI2-CIO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXC 

CO Mass NOx Rate Stk NOXc 

Ib/hr Ib/mmBtu ppm 

0-100 0-1 0-300 

4.44 0.008 2.08 

G12-C7 G12-CB 

2>Stk CDc 2>Gas Flow 

Stk COc Gas hscfh 

ppm 

0-1000 

2.23 

hscfh 

0-10000 

8456.4 

7719.6 

7945.8 

7572.6 

4819.8 

2611.2 

3601.2 

5721.0 

7315.8 

7603.8 

7414.8 

7608.6 

7608.6 

7638.6 

7610.4 

7630.2 

7608.0 

7644.0 

7633.2 

7621.2 

7639.2 

7596.6 

6117.0 

3460.2 

3057.0 

3952.8 

6242.4 

8311.2 

8424.6 

8418.0 

GI2-CIS 

2>NH) Inj 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110. 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

G12-C 

2>MW La 

MW La 

0-1 

102. 

92 .. 

98. : 

90. : 

4S. : 

16 .. 

32. : 

65. 

89.1 

93.1 

89 .. 

92.1 

92 .. 

92 

93.1 

93 . . 

92. : 

93. : 

93.: 

92. : 

93 . . 

92. ! 

66.1 

2S. ' 

22 .. 

36.1 

71.: 

101.: 

102. 

102.1 

Pag~ 
G:;oup#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

01/30/2013 14:15 

01/30/2013 14:16 

01/30/2013 14:17 

01/30/2013 14:18 

01/30/2013 14:19 

01/30/2013 14:20 

01/30/2013 14:21 

01/30/2013 14:22 

01/30/2013 14:23 

01/30/2013 14:24 

01/30/2013 14:25 

01/30/2013 14:26 

01/30/2013 14:27 

01/30/2013 14:28 

01/30/2013 14:29 

01/30/2013 14:30 

01/30/2013 14:31 

01/30/2013 14:32 

01/30/2013 14:33 

01/30/2013 14:34 

01/30/2013 14:35 

01/30/2013 14:36 

01/30/2013 14:37 

01/30/2013 14:38 

01/30/2013 14:39 

01/30/2013 14:40 

01/30/2013 14:41 

01/30/2013 14:42 

01/30/2013 14:43 

01/30/2013 14:44 

01/30/2013 14:45 

01/30/2013 14:46 

01/30/2013 14:47 

01/30/2013 14:48 

01/30/2013 14:49 

01/30/2013 14:50 

01/30/2013 14:51 

01/30/2013 14:52 

01/30/2013 14:53 

01/30/2013 14:54 

Date/Time Printed: 

G12-C2 G12-C4 G12 - Cl1 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 

2.S 

2.6 

2.S 

2.6 

2.6 

2.6 

2.7 

2.S 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

Stk 02 

% 

0-25 

12.95 

12.95 

12.95 

12.95 

12.94 

12.96 

12.95 

12.97 

12.96 

12.96 

12.96 

12.97 

12.96 

12.96 

12.95 

12.95 

12.96 

12.95 

12.94 

12.94 

12.95 

12.95 

12.94 

12.95 

12.95 

12.95 

12.95 

01/31/2013 12,03 

NOx Mass 

1b/hr 

0-100 

6.20 

6.19 

6.19 

6.19 

6.18 

6.18 

6.16 

6.17 

6.17 

6.17 

6.17 

6.17 

6.17 

6.18 

6.18 

6.18 

6.18 

6.18 

6.19 

6.19 

6.18 

6.18 

6.19 

6.17 

6.19 

6.19 

6.18 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0 - 300000 

21235 

21242 

21261 

21234 

20986 

20288 

20251 

20273 

20280 

20282 

20282 

20258 

20284 

20288 

20238 

2026 1 

20234 

20205 

20232 

20167 

20225 

20210 

20206 

20207 

20224 

20197 

20249 

20228 

20231 

20237 

20231 

20210 

20212 

20218 

20215 

20218 

20197 

20261 

20254 

20215 

G12-C3 

2>Stk CO 

Stk co 

ppm 

0-1000 

2.0 

1.9 

1.9 

2.0 

1.9 

1.9 

1.8 

1.8 

1.6 

1.6 

1.7 

1.7 

loS 

1.6 

1.5 

1.6 

1.4 

1.5 

1 5 

loS 

1.6 

1.7 

1.7 

1.5 

1.7 

1.5 

1.4 

G12-C13 G12 -ClO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

1b/hr 

0-100 

2.66 

2.65 

2.65 

2.65 

2.65 

2.65 

2.64 

2.64 

2.64 

2.64 

2.64 

2.64 

1. 76 

2.65 

1. 77 

2.65 

1. 77 

1. 77 

1. 77 

1. 77 

2.65 

2.65 

2.65 

1. 76 

2.65 

1. 77 

1. 77 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 86 

1. 93 

1. 86 

1. 93 

1. 93 

1. 93 

2.00 

1. 86 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

1. 93 

2.00 

2.00 

1. 93 

2.00 

2.00 

2.00 

G12-C7 G12 - C8 

2>Stk COc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1.48 

1.41 

1.41 

1 48 

1.41 

1.41 

1. 34 

1. 34 

1.19 

1.19 

1. 26 

1 26 

1.11 

1.19 

1.11 

1.19 

1. 04 

1.11 

1.11 

1.11 

1.19 

1. 26 

1. 26 

1.11 

1. 26 

1.11 

1. 04 

8421.0 

8434.8 

8431.2 

8454.0 

8421.0 

8427.6 

8433.6 

8421 . 6 

8445.6 

8425.2 

8425.2 

8415.0 

8425.8 

8438.4 

8417.4 

8427.0 

8415.6 

8414.4 

8404.2 

8388.0 

8391.0 

8395.2 

8393.4 

8394.0 

8390.4 

8389.8 

8411. 4 

8413.2 

8414.4 

8406.6 

8414.4 

8416.2 

8417.4 

8409.0 

8407.8 

8419.8 

8400.6 

8427.0 

8424.0 

8407.8 

G12 - C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

l10.0 

110.0 

110.0 

l10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110. a 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1 1 0.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

102.: 

102 .. 

102.: 

102.: 

102. ! 

102. ! 

102. : 

102. ' 

102 .. 

102 .. 

102. : 

102. 

102. 

103. : 

102. 

102 .. 

102 

102 .. 

102.: 

101. 

102. : 

102. ! 

102. : 

101. : 

101 .. 

102.1 

102.: 

102. : 

102.: 

102. ~ 

102. 

102. 

102. 

102 . . 

102. 

102.1 

102. I 

102 . ~ 

102 .. 

102. 

PagE 
Gj:.-oup#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

01/30/2013 14:55 

01/30/2013 14:56 

01/30/2013 14:57 

01/30/2013 14:58 

01/30/2013 14:59 

01/30/2013 15:00 

01/30/2013 15:01 

01/30/2013 15:02 

01/30/2013 15:03 

01/30/2013 15:04 

01/30/2013 15:05 

01/30/2013 15:06 

01/30/2013 15:07 

01/30/2013 15:08 

01/30/2013 15:09 

01/30/2013 15:10 

01/30/2013 15:11 

01/30/2013 15:12 

01/30/2013 15:13 

01/30/2013 15:14 

01/30/2013 15;15 

01/30/2013 15:16 

01/30/2013 15:17 

01/30/2013 15:18 

01/30/2013 15:19 

0 1 /30/2013 15:20 

01/30/2013 15:21 

01/30/2013 15:22 

01/30/2013 15:23 

01/30/2013 15:24 

01/30/2013 15:25 

01/30/2013 15:26 

01/30/2013 15:27 

01/30/2013 15:28 

01/30/2013 15:29 

01/30/2013 15:30 

01/30/2013 15:31 

01/30/2013 15:32 

01/30/2013 15:33 

01/30/2013 15:34 

Date/Time Printed: 

G12-C2 G12-C4 G12-Cll 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.8 

2.7 

2.7 

2.7 

2.7 

2.8 

2.8 

2.7 

Stk 02 

% 

0-25 

12.96 

12.94 

12.95 

12.95 

12.96 

12.96 

12.95 

12.95 

12.95 

12.95 

12.95 

12.96 

12.96 

12.97 

12.96 

12. 96 

12.96 

12.96 

12.96 

12.95 

12.96 

12 .94 

12.94 

12 .95 

12.95 

12.95 

12.95 

12.95 

12.95 

12 .9 5 

12 .94 

12.96 

12.93 

12.93 

12.92 

12.93 

12.93 

12.91 

12.92 

12 . 92 

01/31/2013 12,03 

NOx Mass 

1b/hr 

0-100 

6.18 

6.18 

6.18 

6. 1 8 

6.16 

6.17 

6.17 

6.17 

6.17 

6.18 

6.18 

6.16 

6.17 

6.16 

6.17 

6.17 

6.16 

6.18 

6.17 

6.18 

6.16 

6.18 

6.19 

6.17 

6.18 

6.17 

6.18 

6.18 

6.18 

6.18 

6.19 

6.18 

7.08 

6.20 

6.20 

6.20 

6.20 

7.10 

7.10 

6.21 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20243 

20201 

20222 

20203 

20167 

20197 

20180 

20186 

20189 

20225 

20205 

20174 

20204 

20204 

20200 

20220 

20182 

20236 

20197 

20203 

20190 

20175 

20208 

20172 

20203 

20184 

20213 

20231 

20202 

20222 

20223 

20239 

20216 

20230 

20215 

20220 

20227 

20214 

20235 

20225 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0-1000 

1.6 

1.5 

1.6 

1.6 

1.5 

1.5 

1.6 

1.4 

1.5 

1.4 

1.4 

1.4 

1.5 

1.. 

1.3 

1.5 

1.3 

1.4 

1.5 

1.4 

1.6 

1.3 

1.4 

1.3 

1.4 

1.3 

1.3 

1.5 

1.3 

1.5 

1.4 

1.7 

1.5 

1.5 

1.5 

1.7 

1.7 

2.0 

1.6 

1.9 

G12 -C13 G12-ClO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

2.65 

1. 77 

2.65 

2.65 

1. 76 

1. 76 

2.64 

1. 76 

1. 76 

1. 77 

1. 76 

1. 76 

1. 76 

1. 76 

1. 76 

1. 76 

1. 76 

1. 77 

1. 76 

1. 76 

2.64 

1. 76 

1. 77 

1. 76 

1. 76 

1. 76 

1. 77 

1. 77 

1. 76 

1. 77 

1. 77 

2.65 

1.77 

1. 77 

1. 77 

2.66 

2.66 

2.66 

2.66 

2.66 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.008 

0.008 

0.007 

Stk NOXc 

ppm 

0-300 

1. 93 

2.00 

2.00 

2.00 

1. 93 

2.01 

1. 93 

2.00 

1. 93 

2.00 

2.00 

1. 93 

2.01 

2.01 

2.01 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

2.00 

2.00 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

1. 93 

2.00 

1. 93 

2.07 

2.00 

2.00 

2.00 

2.00 

2.07 

2.07 

2.00 

G12 -C7 G12 -C8 

2>Stk COc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1.19 

1.11 

1.19 

1.19 

1.11 

1.11 

1.19 

1. 04 

1.11 

l. 04 

1. 04 

1. 04 

1.11 

1. 04 

0.97 

1.11 

0.97 

l. 04 

l.11 

1. 04 

1.19 

0.96 

l. 04 

0.96 

l. 04 

0.96 

0.96 

1.11 

0.96 

1.11 

1. 04 

1. 26 

1.11 

1.11 

1.11 

1. 26 

1. 26 

1. 48 

1.18 

1. 40 

8409.0 

8412.6 

8410.8 

8403.0 

8377.2 

8389.8 

8393.4 

8395.8 

8397.0 

8412.0 

8403.6 

8380.2 

8392.8 

8382.0 

8391. 0 

8399.4 

8383.8 

8406.0 

8389.8 

8403.0 

8386.8 

8401.8 

8415.6 

8389.8 

8403.0 

8395.2 

8407.2 

8414.4 

8402.4 

8410 . 8 

8421.6 

8407.2 

8429.4 

8435.4 

8439.6 

8431.2 

8434.2 

8449.8 

8448.0 

8443.8 

G12-C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

102. 

102 .. 

102. ; 

102 .. 

102. 

102 . . 

102. : 

102.1 

102. t 

102. 

102. : 

101. ' 

102 . t 

101. : 

10 2. : 

102 . : 

102.1 

102. 

102. 

102.: 

102.1 

102. ! 

102. : 

102 .. 

102, ' 

102. 

102. : 

102. 

102 .. 

102. : 

102. ! 

102. 

103 .. 

102. : 

102 .. 

102 .. 

102. : 

102. : 

103 .. 

103. t 

PagE 
G:!"oup#-Channel# 

Lo ng Descrip. 

Short Descrip. 

units 

Range 

01/30/2013 15,35 

01/30/2013 15:36 

01/30/2013 15:37 

01/30/2013 15:38 

01/30/2013 15:39 

01/30/2013 15:40 

01/30/2013 15:41 

01/30/2013 15:42 

01/30/2013 15:43 

01/30/2013 15:44 

01/30/2013 15:45 

01/30/2013 15:46 

01/30/2013 15:47 

01/30/2013 15:48 

01/30/ 2 013 15:49 

01/30/2013 15:50 

01/30/2013 15:51 

01/30/2013 15:52 

01/30/2013 15:53 

01/30/2013 15:54 

01/30/2013 15:55 

01/30/2013 15:56 

01/30/ 2 013 15:57 

01/30/2013 15:58 

01/30/2013 15:59 

01/30/2013 16:00 

01/30/2013 16: 01 

01/30/2013 16:02 

01/30/2013 16:03 

01/30/2013 16:04 

01/30/2013 16:05 

01/30/2013 16:06 

01/30/2013 16:07 

01/30/2013 16:08 

01/30/2013 16;09 

01/30/2013 16:10 

01/30/2013 16:11 

01/30/2013 16:12 

01/30/2013 16:13 

01/30/2013 16:14 

Date/Time Printed : 

G12-C2 G12-C4 G12-C11 G12 -C20 

2:>Stk NOx 

Stk NOx 

ppm 

0-150 

2:>Stk 02 2:>NOx Mass 2:>StkFlow 

2.7 

2 .• 

2.7 

2 .• 

2.7 

2.7 

2 .• 

2.7 

2 .• 

2 .• 

2.7 

2.9 

2 .• 

2 .• 

2 .• 

2 .• 

2.7 

2 .• 

2 .• 

2 .• 

2.7 

2 .• 

2 .• 

2 .• 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2 .• 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

Stk 02 

% 

0-25 

12.91 

12.91 

12.92 

12.91 

12.91 

12.91 

12 .8 9 

12 . 90 

12.90 

12.90 

12.91 

12.89 

12.89 

12.88 

12.S9 

12 . B9 

12.92 

12.91 

12.91 

12.91 

12.93 

12.92 

12. 91 

12.92 

12.93 

12.92 

12.93 

12.93 

12.93 

1 2 .94 

12. 93 

12.93 

12.93 

12.93 

12.93 

12.94 

12.94 

1 2 .92 

12 . 93 

12.93 

01/31/2013 12,03 

NOx Mass 

lb/hr 

0-100 

6.21 

7.12 

6.22 

7 .12 

6.23 

6.22 

7.14 

6.24 

7.14 

7.13 

6.23 

7.13 

7.14 

7.16 

7.14 

7.15 

6 . 22 

7.11 

7 .12 

7.12 

6.21 

7.10 

7.11 

7.11 

6.20 

6.20 

6.19 

6.1S 

6.20 

6.18 

6.20 

6.19 

6.21 

7.09 

6.19 

6.18 

6.20 

6.21 

6.20 

6.20 

StkFlow 

ksefh 

0-300000 

20227 

20264 

20254 

20271 

20279 

20257 

20281 

2 0296 

20305 

20276 

20293 

20262 

20274 

20323 

20274 

2 0305 

20255 

20260 

20287 

20290 

20259 

20255 

20257 

20271 

20239 

20215 

20197 

20176 

20220 

20182 

2024 3 

2 0212 

20262 

20236 

20203 

20202 

2 0261 

20239 

20227 

20216 

G12-C3 GI2-C13 GI2-CI0 G12-C6 G12-C7 G12 -C8 G12-C18 GI2-C 

2:>Stk CO 2 :>CO Mass 2:>NOx Rate 2:>Stk NOXe 2:>Stk COc 2:>Gas Flow 2:>NH3 Inj 2:>MW Lo 

Stk co 

ppm 

0-1000 

1.7 

I.. 

1.5 

1 3 

1.7 

1.5 

1.9 

1.9 

2.1 

2.3 

2.' 

2.' 

2.2 

2.' 

2.2 

2.2 

2.3 

2.' 

2.' 

2.' 

2.' 

2.7 

2 .• 

2.5 

2.7 

2.7 

2.9 

2.8 

2.7 

2.7 

2.6 

2.8 

2.7 

2.8 

2.7 

2.8 

2.9 

2.8 

2.9 

2.9 

CO Mass 

lb/hr 

0 -100 

2.66 

2.67 

1. 78 

1. 78 

2.67 

1. 78 

2.68 

2.68 

2.68 

3.56 

3.56 

3.57 

3.57 

3.58 

3.57 

3.57 

3.55 

3.56 

3.56 

3.56 

3.55 

3.55 

4.45 

3.55 

3.54 

3.54 

4.42 

4.42 

3.54 

3.53 

3.55 

4.42 

3.55 

4.43 

3.54 

4.42 

4.43 

4.44 

4.43 

4.43 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.008 

0.007 

0.008 

0.007 

0.007 

0.008 

0.007 

O.OOB 

0.008 

0.007 

0.008 

O.OOS 

O.OOB 

O.OOB 

O. OOB 

0.007 

0.008 

O.OOB 

0.008 

0.007 

0.008 

0 . 008 

O.OOB 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 . 007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0 -3 00 

1. 99 

2.07 

2.00 

2.07 

1. 99 

1. 99 

2.06 

1. 99 

2.07 

2.07 

1. 99 

2.14 

2.06 

2.06 

2.06 

2.06 

2.00 

2.07 

2.07 

2.07 

2.00 

2.07 

2.07 

2.07 

2.00 

2 .00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.07 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

Stk COe Gas hscfh 

ppm hscfh 

0-1000 0 - 10000 

1 . 26 8455.2 

1.33 8470.B 

1.11 84 55.8 

0.96 8473.8 

1.26 8476.8 

1 . 11 8467.8 

1.40 8499.0 

1.40 8494.8 

1.55 8498.4 

1.70 8486.4 

1.77 8482.8 

1.77 8491.2 

1.62 8496.0 

1.77 8527.2 

1 . 62 8496.0 

1 . 62 8509.2 

1.70 8456.4 

1.77 8469.0 

1.77 8480.4 

1.77 8481 .6 

1.78 8447.4 

2.00 8456.4 

2. 07 8467.8 

1 . 85 8463.0 

2.00 8439.0 

2.00 8439.6 

2.15 8421.6 

2.07 8412.6 

2 . 00 8431.2 

2 . 00 8404.8 

1 . 92 B440.8 

2.07 8427.6 

2.00 8448.6 

2.07 8437.8 

2.00 8424.0 

2.08 8413.2 

2.15 8437.8 

2.07 8449.8 

2.15 8434.2 

2.15 8429.4 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110. 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

MW Lo 

0-1 

103.1 

103.: 

103.· 

103.· 

103.: 

103." 

103.~ 

103./ 

103.· 

103.~ 

103.: 

104.1 

104.! 

104.: 

103.: 

104.· 

103.1 

103.· 

03.~ 

1 03.: 

102.: 

103.· 

103.' 

103.1 

103 

103.1 

102. 

102.1 

102.: 

102.: 

102.! 

102.: 

102. 

102.' 

102.~ 

102.: 

102.' 

103.1 

102. 

103.! 

Pag( 
Gr.oup#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

01/30/2013 16:15 

01 / 30/2013 16:16 

01/30/2013 16:17 

01/30/2013 16:18 

01/30/2013 16:19 

01/30/2013 16:20 

01/30/2013 16:21 

01/30/2013 16:22 

01/30/2013 16:23 

01/30/2013 16:24 

01/30/2013 16:25 

01/30/ 2013 16:26 

01/30/2013 16:27 

01/30/2013 16:28 

01/30/2013 16:29 

01/30/2013 16:3 0 

01/30/2013 16:31 

01/30/2013 16:32 

01/30/2013 16:33 

01/30/2013 16:34 

01/30/2013 16:35 

01/30/2013 16:36 

01/30/2013 16:37 

01/30/2013 16:38 

01/30/2013 16:39 

01/30/2013 16:40 

01/30/2013 16:41 

01/30/2013 16:42 

01/30/2013 16:43 

01/ 30/2013 16:44 

01/30/2013 16 :45 

01/30/2013 16:46 

01/30/2013 16:47 

01/30/2013 16:48 

01/30/2013 16:49 

01/30/2013 16:50 

01/30/2013 16:51 

01/30/2013 16:52 

01/30/2013 16:53 

01/30/2013 16:54 

Date/Time Printed: 

G12 - C2 G12 - C4 G12-C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2 >NOx Mass 2>StkFlow 

2.7 

2.7 

2.B 

2.6 

2.7 

2 .B 

2.7 

2.B 

2.7 

2.7 

2 .7 

2.7 

2.7 

2.7 

2.7 

2.B 

2.7 

2.6 

2.6 

2.6 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.B 

2.7 

2.B 

2.B 

2.B 

2.7 

2.B 

2.7 

2.7 

2.7 

2.6 

2.6 

2.7 

2 . 6 

Stk 02 

• 

0-25 

12.91 

12.92 

12.91 

12.94 

12.94 

12.93 

12.93 

12 .93 

12 .94 

12.94 

12.93 

12.93 

12.93 

12.93 

12.92 

12.91 

12.93 

12.93 

12.93 

12.94 

12.94 

12.93 

12.94 

12.94 

12. 93 

12.92 

12.91 

12.91 

12.91 

12.90 

12.90 

12.91 

12.90 

12.92 

12.93 

12.93 

12. 95 

12.94 

12 .94 

12.96 

01/31/2013 12,03 

NOx Mass 

Ib/hr 

0-100 

6.21 

6.21 

7.11 

6.18 

6.18 

7.09 

6.20 

7.09 

6.19 

6.19 

6.20 

6.21 

6.19 

6.20 

6.21 

7.10 

6.20 

6.20 

6.20 

6 . 19 

6.20 

6.21 

6.19 

6.21 

6.20 

6.23 

7.11 

6.23 

7.13 

7.14 

7.13 

6.22 

7.12 

6.23 

6.22 

6.22 

6.20 

6.21 

6.21 

6.19 

StkFlow 

kscfh 

0 - 300000 

20205 

20239 

20243 

20182 

20191 

20252 

20219 

20233 

20210 

20237 

20240 

20252 

20206 

20243 

20249 

20221 

20226 

20213 

20216 

20218 

20248 

20260 

20224 

20277 

20236 

20291 

20260 

20293 

20310 

20305 

20272 

20251 

20243 

20303 

20301 

20308 

20287 

20276 

20277 

20260 

G12 -C3 G12 -C13 G12-C10 G12 - C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

Stk CO 

ppm 

0-1000 

2.B 

2.9 

2.B 

2.9 

3.0 

3.0 

3.0 

2.9 

2.9 

2.9 

3.0 

3.1 

3.1 

3 .1 

3.2 

3.1 

3.2 

3.3 

3.3 

3.2 

3.4 

3.2 

3.1 

3.2 

3.2 

3.2 

3.1 

3.2 

3.1 

3.3 

2.9 

3 . 1 

3.0 

3.1 

3.1 

3.2 

3.3 

3.3 

3.1 

3.4 

CO Mass 

lb/hr 

0-100 

4.43 

4.44 

4.44 

4.41 

4.41 

4.43 

4.43 

4.43 

4.42 

4.42 

4.43 

4.43 

4.42 

4.43 

4.44 

4.44 

4.43 

4.43 

4.43 

4.42 

5.31 

4.44 

4.42 

4.43 

4.43 

4.45 

4.45 

4.45 

4.46 

4.46 

4.45 

4.44 

4.45 

4.45 

4.44 

4.45 

4.43 

4.43 

4.43 

5.30 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.008 

0.007 

0.007 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 99 

2.00 

2.07 

1. 93 

2.00 

2.07 

2.00 

2.07 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.07 

2.00 

1. 92 

1. 92 

1. 93 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.07 

1. 99 

2.07 

2.07 

2.07 

1. 99 

2.07 

2.00 

2.00 

2.00 

1. 93 

1. 93 

2.00 

1. 93 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

2.07 

2.14 

2.07 

2 . 15 

2 .2 2 

2.22 

2 . 22 

2.15 

2.15 

2.15 

2.22 

2.29 

2.29 

2.29 

2.37 

2.29 

2.37 

2.44 

2.44 

2.37 

2 . 52 

2.37 

2.30 

2.37 

2.37 

2.37 

2.29 

2.36 

2.29 

2.43 

2.14 

2.29 

2.21 

2.29 

2.29 

2.37 

2.45 

2.45 

2.30 

2.53 

8446.2 

8449.8 

8461.8 

8404.8 

8408.4 

8444.4 

8430.6 

8436 .6 

8416.2 

8427.6 

8439.6 

8444.4 

8425.2 

8440.8 

8454.0 

8452.8 

8433.6 

8428.2 

8429.4 

8419.8 

8432.4 

8448.0 

8422.2 

8444.4 

8437.8 

8471. 4 

8469.0 

8482.8 

8490.0 

8498.4 

8484.6 

8465.4 

8472.6 

8476.2 

8464.8 

8467.8 

8437.8 

8443.8 

8444.4 

8416.2 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

llO. a 

110.0 

2>Summary - I-Min RATA - Continued 

MW Lo 

0-1 

102. ; 

103.1 

103.1 

101 .. 

102. 

103.1 

102 . . 

102 .. 

102. ! 

102.: 

103.· 

102.' 

102. · 

103.: 

102.' 

102. ; 

102. ! 

102 . . 

102. : 

102 .. 

102. 

102 

102 . . 

102 .. 

102. 

103 

103. : 

103. I 

103. 

103 .. 

103. r 

103. I 

103. I 

103. I 

102 .. 

102. ' 

102.: 

102.' 

102.' 

102.1 

PagE 
Gr oupfr-Channel# 

Long Descrip . 

Short Descrip . 

Units 

Range 

01/30/2013 16:55 

01/30/2013 16:56 

01/30/2013 16:57 

01/30/ 2 013 16:58 

01/30/ 2013 16:59 

01/30/2013 17:00 

01/30/2013 17:01 

01/30/2013 17:02 

0 1/30/2013 17:03 

01/30/2013 17:04 

01/30/ 2013 17:05 

01/30/ 2013 17:06 

01/30/2013 17:07 

01/30/2013 17:08 

01/30/2013 17:09 

01/30/2013 17:10 

01/30/2013 17:11 

01/30/2013 17:12 

01/30/ 2013 17:13 

01/30/2013 17:14 

01/30/2013 17 :15 

01/30/2013 17:16 

01/30/2013 17:17 

01/30/2013 17:18 

01/30/2013 17:19 

01/30/ 2013 17:20 

01/30/2013 17:21 

01/30/2013 17:22 

0 1 /30/2013 17:23 

01/30/2013 17:24 

01/30/2013 17:25 

01/30/2013 17:26 

01/30/2013 17:27 

01/30/ 2 013 17:28 

01/30/2013 17:29 

01/30/2013 17:30 

01/30/2013 17:31 

01/30/2013 17:32 

01/30/2013 17:33 

01/30/2013 17:34 

Date/Time Printed: 

G12-C2 G12-C4 G12 -C11 G12-C20 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 2>StkFlow 

2.7 

2.6 

2.7 

2.6 

2.6 

2.6 

2.7 

2.7 

2.7 

2.7 

2 . 6 

2.7 

2.7 

2.B 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2 . 7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.B 

2.7 

2.7 

Stk 02 

• 

0-25 

12.95 

12.97 

12.96 

12 . 97 

12.96 

12.95 

12.94 

12.93 

12.93 

12.93 

1 2.93 

12.92 

12 .9 3 

12.92 

1 2.93 

12.91 

12.92 

1 2 .92 

12.93 

12.93 

12.93 

12 .92 

12.92 

12.92 

12.93 

12.93 

12.91 

12.93 

12.92 

12.94 

12. 93 

12.93 

12.93 

12 . 93 

12 .93 

12.92 

12,-91 

12.91 

12.91 

12.92 

01/31/2013 12,03 

NOx Mass 

Ib/hr 

0 -100 

6.18 

6.16 

6.16 

6.16 

6.16 

6.18 

6.20 

6.21 

6 .21 

6.21 

6.23 

6.24 

6.23 

7.13 

6.23 

6.25 

6.25 

6.24 

6.24 

6.22 

6.23 

6.24 

6.23 

6.25 

6.23 

6.24 

6.25 

6.25 

6.24 

6.23 

6.23 

6.23 

6.23 

6.23 

6.24 

6.25 

6.25 

7.16 

6.24 

6.24 

StkFlow 

kscfh 

0 -30 0000 

20215 

20189 

2017 4 

20195 

20184 

20208 

20238 

20255 

20255 

20255 

20321 

20323 

20334 

20321 

20340 

20342 

20353 

20343 

20345 

20291 

20322 

20340 

20316 

20362 

20325 

20377 

20336 

20383 

20347 

20351 

20318 

20325 

20322 

20314 

20358 

20367 

20339 

20378 

20317 

20340 

G12-C3 G12 - C13 G12 -CI0 G12 -C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

stk CO 

ppm 

0-1000 

3.4 

3.4 

3.9 

3.7 

3.6 

3 .7 

3.6 

3.3 

3.3 

3.3 

3.5 

3 .4 

3.6 

3.3 

3.6 

3.5 

3.6 

3.6 

3.6 

3.B 

3.9 

3.7 

3.B 

3.B 

3.6 

3.B 

3.6 

3.B 

3.6 

3.7 

3.7 

3.6 

3 . 7 

3.6 

4.0 

3.B 

3.B 

3 .4 

3 .B 

3.6 

CO Mass 

Ib/hr 

0-100 

5.30 

5.28 

5.28 

5.28 

5.28 

5.30 

5 . 31 

4.43 

4.43 

4.43 

5.34 

5.35 

5.34 

4 .45 

5.34 

5.36 

5.35 

5.35 

5.34 

5.33 

5.34 

5 .3 5 

5.34 

5.36 

5.34 

5 .3 5 

5.36 

5.35 

5.35 

5.34 

5.34 

5.34 

5.34 

5.34 

6.24 

5.36 

5.36 

5.37 

5.35 

5.35 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0 .0 07 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

2.00 

1. 93 

2.01 

1. 93 

1. 93 

1. 93 

2.00 

2.00 

2.00 

2.00 

1. 92 

2.00 

2.00 

2.07 

2.00 

1. 99 

1. 92 

2.00 

1. 92 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

2.00 

1. 99 

2.00 

1. 92 

2.00 

2.00 

1. 92 

2.00 

2.00 

1. 92 

2.00 

1. 99 

2.07 

1. 99 

2.00 

Stk COc Gas hscfh 

hscfh 

0-10000 

ppm 

0-1000 

2.52 

2.53 

2.90 

2. 75 

2.68 

2.75 

2.67 

2 . 44 

2.44 

2.44 

2. 59 

2 .51 

2.66 

2.44 

2.66 

2.58 

2.66 

2.66 

2.66 

2.81 

2.89 

2.74 

2.81 

2.81 

2.66 

2.81 

2.66 

2 .81 

2.66 

2.74 

2.74 

2.66 

2. 74 

2.66 

2.96 

2.81 

2.81 

2.51 

2.81 

2.66 

8407.8 

8376.0 

8380.2 

8378.4 

8384.4 

8404.8 

8428.2 

8445.6 

8445.6 

8445.6 

8473.2 

8484.6 

8478.6 

8484.0 

8481 . 0 

8503.2 

8497.2 

8493.0 

8483.4 

8460 . 6 

8473.8 

8491.8 

8481. 6 

8500.8 

8475.0 

8496.6 

8500.8 

8499.0 

8494.8 

8475.0 

8472.0 

8475.0 

8473.8 

8470.2 

8488.8 

8503.2 

8502.0 

8518 . 2 

8493.0 

8491. 8 

NH31I1j 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

l10.0 

110.0 

110 .0 

110.0 

110.0 

l10. 0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

2>Summary - 1-Min RATA - Continued 

MW La 

0-1 

102. : 

101. ! 

101.! 

101. : 

102. t 

102. : 

102 . . 

103.1 

103 . t 

103.1 

103. t 

103.! 

103. : 

104.1 

102. 

103. : 

103. ! 

103. ' 

103 . : 

102 

103. : 

103. t 

103. t 

103 

103. ! 

103.: 

103. ! 

103. : 

103.! 

103.1 

102. : 

102. : 

103. t 

103.: 

103. 

103.! 

10 3 .' 

103.: 

103.· 

103.: 

PagE 
G:::-oupfr - Channel# 

Long Descrip . 

Short Descrip . 

units 

Range 

01/30/2013 17:35 

01/30/2013 17:36 

01/30/2013 17:37 

01/30/2013 17:38 

01/30/2013 17:39 

01/30/2013 17:40 

01/30/2013 17: 41 

01/30/2013 17:42 

01/30/2013 17:43 

01/30/2013 17:44 

01/30/2013 17:45 

01/30/2013 17:46 

01/30/2013 17:47 

01/30/2013 17:48 

01/30/2013 17;49 

01/30/2013 17:50 

01/30/2013 17:51 

Period Average 

Period Max Value 

Period Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12-C2 G12-C4 G12 -C11 G12-C20 G12-C3 G12 -CD GI2-CI0 G12 -C6 G12-C7 G12-C8 G12-C18 G12-C 

2>Stk NOx 

Stk NOx 

2>stk 02 2>NOx Mass 2>StkFlow 2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW Lo 

ppm 

0-150 

2.8 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.8 

2.7 

2.7 

2.6 

2.6 

2.6 

2.7 

2.6 

Stk 02 

• 

0-25 

12.91 

12.93 

12.93 

1 2.92 

12.92 

12 . 92 

12.91 

1 2.91 

12.92 

12.92 

12 .91 

12. 91 

12.93 

12.93 

12.94 

12. 94 

12.96 

NOx Mass 

1b/hr 

0- 100 

7.15 

6.24 

6.25 

6.26 

6.26 

6.27 

6.28 

6.27 

6.26 

7.15 

6.27 

6.25 

6.24 

6.23 

6.23 

6.23 

6.20 

StkFlow 

kscfh 

0-300000 

20356 

20361 

20393 

20400 

20405 

20428 

20429 

20424 

20409 

20379 

20401 

20339 

20367 

20317 

20342 

20346 

20323 

Stk CO 

ppm 

0-1000 

3.7 

3.7 

3 . 9 

3.7 

3 . 7 

3.8 

3.6 

4.0 

3.7 

4. 0 

3.8 

3.8 

3.7 

3.9 

3.9 

3.8 

4.0 

2.7 12.93 6.36 20054 2.6 

2.9 12.97 7.16 21261 4.0 

2.5 12.88 6.16 9923 1.3 

5.5080E+2 2.6511E+3 1.3028E+3 4.9533E+6 5.3740E+2 

83.3 83 .3 83.3 100.0 83.3 

01/31/2013 12,03 

CO Mass 

lb/hr 

0-100 

5.36 

5.35 

5.36 

5.37 

5.37 

5.37 

5.38 

6.27 

5.37 

6.25 

5.37 

5.36 

5.35 

5.34 

5.34 

5.34 

6.20 

NOx Rate 

lb/mmBtu 

0 - 1 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

0.007 

Stk NOXc 

ppm 

0 - 300 

2.07 

2.00 

2.00 

2.00 

2.00 

2.00 

1. 99 

1. 99 

2.00 

2.07 

1. 99 

1. 99 

1. 92 

1.92 

1. 93 

2.00 

1. 93 

3.77 0.007 1.99 

6.27 0.008 2.14 

1.76 0.007 1 .8 6 

7.7227E+2 1.4689E+O 4.0786E+2 

83.3 83.3 83.3 

Stk COc Gas hscfh 

ppm 

0-1000 

2.73 

2.74 

2.89 

2. 74 

2.74 

2.81 

2.66 

2.95 

2.74 

2.96 

2 .81 

2.81 

2.74 

2.89 

2.89 

2.82 

2.97 

hscfh 

0-10000 

8509.2 

8490.0 

8503.2 

8517.0 

8518.8 

8528.4 

8539.8 

85 37 .4 

8520.6 

8508.0 

8527.8 

8502.0 

8492.4 

8471.4 

8471. 4 

8473.2 

8442.0 

NH3Inj 

lb/hr 

0 - 1000 

l10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

l10.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

MW Lo 

0-1 

103.: 

103. 

104 . 1 

103.' 

104.1 

104.: 

104 .: 

103. ' 

104. 1 

103 

103.' 

103.' 

103.' 

103.' 

102.' 

103.1 

102.: 

1 . 94 8239.1 110.0 99.8 

2 .97 8539.8 110.0 104. 

0.96 2611.2 110.0 16. 

3.9779E+2 2.0350E+6 2.7170E+4 2.4671E+ 

83.3 100.0 100.0 100 . 

2>Summary - I-Min RATA - Continued PagE 
Data Summary Report 

Company : CPV Sentinel, LLC 

62575 Powerline Road 

Desert Hot Springs, CA 92240 

c~ ~(()' \J ;',f-1.. _ TRACE -

Source : Turbine 2 

Data Group : 2>1-Min Cales 

~ 

., 5-L/~(L- fM- toO-3 

Ellvironmenlal S y slems, Ill c. 

Report Name : 

Start of Report : 

2>Summary - I-Min RATA 

01/31/2013 OS,33 

G12-C4 

End of Report, 01/31/2013 12,39 

GI2-Cll G12-C20 G12-C3 G12-C13 

validation: All Available Data 

Group#-Channel# GI2-Cla G12-C6 G12-C7 G12-Ca GIZ-C18 G12-C 

Long Descrip. 

Short Descrip. 

Units 

G12-C2 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkFlow 2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXc 2>Stk COc 2>Gas Flow 2>NH3 Inj 2>MW La 

Range 

01/31/2013 08:33 

01/31/2013 08:34 

01/31/ 2013 08:35 

01/3 1 /2013 08:36 

01/31/2013 08:37 

01/31/2013 08:38 

01/31/2013 08:39 

01/31/2013 08:40 

01/31/2013 08:41 

01/31/2013 08:42 

01/31/2013 08:43 

01/31/2013 08:44 

01/31/2013 08:45 

01/31/2013 08:46 

01/31/2013 08:47 

01/31/2013 08:48 

01/31/2013 08:49 

01/31/2013 08:50 

01/31/2013 08:51 

01/31/2013 08:52 

01/31/2013 08:53 

01/31/2013 08:54 

01/31/2013 08:55 

01/31/2013 08:56 

01/31/2013 08:57 

01/31/2013 08:58 

01/31/2013 08:59 

01/31/2013 09:00 

01/31/2013 09:01 

01/31/2013 09:02 

Date/Time Printed: 

2.8 

2.7 

2 .8 

2.8 

2.8 

2.8 

2.7 

2.7 

2.7 

2.7 

2.8 

2.7 

2. 8 

2.7 

2.7 

2.8 

2.7 

2.8 

2.7 

2.7 

2.7 

2.8 

2 . 8 

2.8 

2.7 

2.6 

2.7 

2.8 

2.7 

2.7 

Stk 02 

• 

0-25 

13.20 

13.21 

13. 2 0 

13.20 

13.21 

13 .20 

13 .20 

13 . 19 

13 .19 

13 .20 

13 .19 

13.19 

13 .19 

13.20 

13 .20 

13.20 

13.21 

13 . 1 9 

13 .1B 

13 .18 

13 .19 

13 .19 

13 .18 

13 .18 

13 .18 

13 .19 

13.20 

13 .19 

13 . 19 

13 . 20 

01/31/2013 13,29 

NOx Mass 

Ib/hr 

0-100 

6.96 

6.93 

6.95 

6.94 

6.95 

6.96 

6.95 

6.96 

6.95 

6.94 

6.96 

6.96 

6.95 

6 . 95 

6.94 

6.94 

6.96 

6.97 

6.99 

6.99 

6.97 

6.98 

6.97 

6.97 

6.96 

6.06 

6.93 

6.94 

6.96 

6.94 

StkFlow 

kscfh 

0-300000 

20554 

20499 

20526 

20518 

20566 

20554 

20546 

20535 

20499 

20517 

20532 

20527 

20503 

20546 

20524 

20517 

20584 

20578 

20612 

20600 

20575 

20606 

20551 

20548 

20501 

20445 

20485 

20491 

20530 

20509 

Stk CO 

ppm 

0-1000 

3.2 

2.9 

2.6 

2.7 

2.9 

2.9 

2.9 

2.6 

2.7 

2.7 

2.S 

2.8 

2.6 

2.4 

2.7 

2.3 

2.8 

2.5 

2.3 

2.4 

2.6 

2.5 

2.4 

2.4 

2.5 

2.S 

2.6 

2.7 

2.7 

2.7 

CO Mass 

1b/hr 

0 - 100 

4.35 

4.33 

3.47 

4.34 

4.34 

4.35 

4.35 

3.48 

4.34 

4.34 

3.48 

4.35 

3.47 

3.48 

4.34 

3.47 

4.35 

3.49 

3.50 

3.49 

3.49 

3 . 49 

3.49 

3.49 

3.48 

3.46 

3.47 

4.34 

4.35 

4.34 

NOx Rate 

Ib/mmStu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

O.OOB 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0 . 008 

0 . 008 

0.008 

0.007 

0.008 

O.OOB 

0.008 

0.008 

Stk NOXc 

ppm 

0-300 

2.15 

2.07 

2.15 

2.15 

2.15 

2.15 

2.07 

2 . 07 

2.07 

2.07 

2.14 

2.07 

2.14 

2.07 

2.07 

2.1S 

2.07 

2.14 

2 . 06 

2.06 

2.07 

2.14 

2.14 

2.14 

2.06 

1. 99 

2.07 

2 . 14 

2.07 

2.07 

stk CDc Gas 

ppm 

0-1000 

2.45 

2.22 

1. 99 

2.07 

2.22 

2.22 

2.22 

1. 99 

2.07 

2.07 

1. 91 

2.14 

1. 99 

1. 84 

2.07 

1. 76 

2.15 

1. 91 

1. 76 

1. 83 

1. 99 

1. 91 

1. 83 

1. 83 

1. 91 

1. 91 

1. 99 

2.07 

2 . 0 7 

2 . 07 

hscfh 

hscfh 

0-10000 

8280.0 

8247.0 

8268 .6 

8265 . 6 

8274.0 

8280.0 

8277.0 

8283.0 

8268.6 

8265.0 

8281. 8 

8280.0 

8270.4 

8277 . 0 

8268 . 0 

8265.0 

8281. 2 

8300.4 

8325.0 

8320 . 2 

8299.2 

8311.8 

8300.4 

8299 . 2 

8280.0 

8247.0 

8252.4 

8265 . 6 

8281 .2 

8262.0 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

MW La 

0-1 

100.1 

99. 

99. 

99 .. 

99. : 

99. 

100 .. 

100. 

99 . . 

99 .. 

100 .. 

100 .. 

99 .. 

100 .. 

99 .. 

100.1 

100. ! 

100 

100 .. 

100 .. 

100.: 

100 .. 

100 . . 

100. ! 

100 .. 

99 .. 

99. 

100.1 

99. 

99 . . 

pagE 
Group#-Channe l# 

Long Descrip . 

Short Des c r ip . 

Units 

Range 

01/31/2013 09:03 

01/31/2013 09:04 

01/31/2013 09:05 

01/31/2013 09:06 

01/31/2013 09:07 

01/31/2013 09:08 

01/31/2013 09:09 

01/31/2013 09:10 

01/31/2013 09:11 

01/31/2013 09:12 

01/31/2013 09:13 

01/31/2013 09:14 

01/31/2013 09:15 

01/31/2013 09:16 

01/31/2013 09:17 

01/31/2013 09:18 

01/31/2013 09:19 

01/31/2013 09:20 

01/31/2013 09:21 

01/31/2013 09:22 

01/31/2013 09:23 

01/31/2013 09:24 

01/31/2013 09:25 

01/31/2013 09:26 

01/31/2013 09:27 

01/31/2013 09:28 

01/31/2013 09:29 

01/31/2013 09:30 

01/31/2013 09:31 

01/31/2013 09:32 

01/31/2013 09:33 

01/31/2013 09:34 

01/31/2013 09:35 

01/31/2013 09:36 

01/31/2013 09:37 

01/31/2013 09:38 

01/31/2013 09:39 

01/31/2013 09:40 

01/31/2013 09:41 

01/31/2013 09:42 

Date/Time Printed: 

G12-C2 G12 -C4 GI2 - Cll 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>stk 02 2>NOx Mass 

2.7 

2.8 

2.8 

2.7 

2.6 

2.7 

2.7 

2.7 

2.7 

2.8 

2.7 

2.7 

2.8 

2.7 

2.7 

2.8 

2.9 

2.7 

2.8 

2.8 

2.8 

2.7 

2.8 

2.7 

2.8 

2.8 

2 . 7 

2.7 

2.8 

2.7 

2.7 

2.7 

2.7 

2.8 

2.6 

2.8 

2.7 

2.6 

2.7 

2.7 

Stk 02 

• 

0-25 

13.20 

13 .18 

13 .18 

13 .18 

13.18 

13 .19 

13 .19 

13.18 

13 .17 

13 .17 

13 .18 

13 .18 

13 .17 

13 .1B 

13 . 1B 

13 .18 

13 .14 

13 .13 

13 .14 

13 .14 

13 .15 

13 .15 

13 .16 

13 .17 

13 .16 

13 .17 

13 .17 

13 .17 

13 .17 

13 .19 

13 .2 0 

13.21 

13.21 

13 .19 

13 .19 

13 .19 

13 .19 

13.1B 

13 . 19 

13 .1B 

01/31/2013 13,29 

NOx Mass 

1b/hr 

0-100 

6.95 

7.00 

7.00 

7.00 

6.11 

6.9B 

6.9B 

6.98 

6.99 

6.98 

6.97 

6.97 

6.97 

6.97 

6.97 

6.96 

7.06 

7.06 

7.05 

7.05 

7.02 

7.01 

7.00 

7.00 

6.98 

6.98 

6.97 

6.96 

6.96 

6.95 

6.93 

6.92 

6.91 

6.95 

6.07 

6.95 

6.95 

6.08 

6.94 

6.94 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20530 

20619 

20631 

20642 

20597 

20600 

20608 

20582 

20573 

20533 

20554 

20542 

20516 

20530 

20542 

20523 

20716 

20662 

20686 

20662 

20621 

20572 

20585 

20603 

20525 

20557 

20516 

20483 

20490 

20509 

20481 

20479 

20457 

20505 

20484 

20520 

20506 

20492 

20489 

20453 

G12-C3 

2>Stk CO 

Stk CO 

ppm 

0 - 1000 

2.8 

2.S 

2.6 

2.S 

2.6 

2.7 

2.E:! 

2.7 

2.7 

2.7 

2.9 

3.0 

2.7 

2.9 

3.0 

2.8 

2.9 

2.7 

2.6 

2.7 

2.S 

2.9 

3.2 

3.3 

3.4 

3.S 

3.S 

3.6 

3.3 

3.6 

3.9 

3.9 

3.8 

3.S 

3.7 

3.8 

3.8 

3 . 7 

3.8 

3.8 

G12 - C13 G12-C10 G12 - C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

lb/hr 

0-100 

4.34 

3.50 

3.50 

3.50 

3.49 

4.36 

3.49 

4 . 36 

4.37 

4.36 

4.36 

4.36 

4.36 

4.35 

4.36 

4.35 

4.42 

4.41 

3.53 

4.40 

3.51 

4.38 

4.38 

5.25 

5.24 

5.24 

5.23 

5.22 

5.22 

5.21 

6.06 

6.06 

6.05 

5.21 

5.21 

6.08 

6.08 

5.21 

6.07 

6.07 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0 . 008 

0 . 008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

O.OOB 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

O.OOB 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.007 

0.008 

0.008 

Stk NOXc 

ppm 

0 - 300 

2.07 

2.14 

2 . 14 

2.06 

1 : 99 

2.07 

2.07 

2.06 

2.06 

2.14 

2.06 

2.06 

2.14 

2.06 

2.06 

2.14 

2.20 

2.05 

2.13 

2.13 

2.13 

2.06 

2.13 

2.06 

2.13 

2.14 

2.06 

2.06 

2.14 

2.07 

2.07 

2.07 

2.07 

2.14 

1. 99 

2.14 

2.07 

1. 99 

2.07 

2.06 

G12-C7 G12-C8 

2>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hsefh 

0-1000 0 - 10000 

2.15 

1. 91 

1. 99 

1. 91 

1. 99 

2.07 

1. 99 

2.06 

2.06 

2.06 

2.22 

2.29 

2.06 

2.22 

2 . 29 

2.14 

2.20 

2.05 

1. 98 

2.05 

1. 90 

2.21 

2. 44 

2.52 

2.59 

2.67 

2.67 

2.75 

2.52 

2.75 

2.99 

2.99 

2.92 

2.68 

2.83 

2.91 

2.91 

2.83 

2.91 

2.90 

8270.4 

8328.0 

8332.8 

8337.0 

8319.0 

8309.4 

8312.4 

8313.0 

8320.2 

8304.0 

8301.6 

8296.8 

8296.8 

8292.0 

8296.8 

8289.0 

8410.2 

8399.4 

8398.2 

8388.6 

8361.0 

8341.2 

8335.8 

8332.2 

8311.2 

8313.6 

8296.8 

8283.6 

8286.6 

8272.8 

8250.6 

8239.2 

8230.2 

8271.0 

8262.6 

8277.0 

8271.6 

8276.4 

8264.4 

8260.8 

G12-C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1l0.0 

1l0. a 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1l0.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

99 .. 

100. 

100 . . 

101.1 

100. : 

99. : 

100 . 

100 .. 

100. 

100. : 

100 . . 

99. ; 

100. t 

99. : 

100. : 

100.: 

101. . 

101 .. 

101. 

101. 

101 

100. : 

100. 

101 .. 

100. : 

100 .. 

99. : 

100 .: 

100 .. 

99 .. 

99. 

99. 

99.1 

99.: 

99. ! 

100. t 

99. : 

99.! 

99 .. 

99. ! 

Pag( 
Group#-Channe l # 

Long Descrip . 

Short Descrip . 

Units 

Range 

01/31/2013 09:43 

01/31/2013 09:44 

01/31/2013 09:45 

01/31/2013 09:46 

01/31/2013 09:47 

01/31/2013 09:48 

01/31/2013 09:49 

01/31/2013 09:50 

01/31/2013 09:51 

01/31/2013 09:52 

01/31/2013 09:53 

01/31/2013 09:54 

01/31/2013 09:55 

01/31/2013 09:56 

01/31/2013 09:57 

01 / 31/2013 09:58 

01/31/2013 09:59 

01/31/2013 10:00 

01/31/2013 10:01 

01/31/2013 10:02 

01/31/2013 10:03 

01/31/2013 10:04 

01/31/2013 10:05 

01/31/2013 10:06 

01/31/2013 10:07 

01/31/2013 10:08 

01/31/2013 10:09 

01/31/2013 10:10 

01/31/2013 10:11 

01/31/2013 10:12 

01/31/2013 10:13 

01/31/2013 10:14 

01/31/2013 10:15 

01/31/2013 10:16 

01/31/2013 10:17 

01/ 31/2013 10:18 

01/31/2013 10:19 

01/31/2013 10:20 

01/31/2013 10:21 

01/31/2013 10:22 

Date/Time Printed: 

G12-C2 G12-C4 G12-Cl1 G12 - C20 

2>Stk NOx 

Stk NOx 

2>Stk 02 2 >NOx Mass 2 >StkFlow 

ppm 

0-150 

2.9 

2.7 

2.7 

2.7 

2.8 

2.7 

2.7 

2.6 

2.7 

2.7 

2.8 

2.8 

2.7 

2.7 

2.7 

2.7 

2.8 

2.7 

2.8 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.8 

2.8 

2.8 

2.7 

2.8 

2.7 

2.6 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.6 

2.7 

stk 02 

• 

0-25 

13 .17 

13 .17 

13 .18 

13 .19 

13 .19 

13 .19 

13 .19 

13 .19 

13 .18 

13 .19 

13 .19 

13 .19 

13 .18 

13 .19 

13 .17 

13 .18 

13 .18 

13 . 17 

13 .17 

13 .17 

13 .17 

13 .16 

13 .16 

13 .16 

13 .17 

13 .16 

13.15 

13 .15 

13 .14 

13 .15 

13 .16 

13 .16 

13 .16 

13 . 17 

13 .16 

13.17 

13.16 

13.17 

13 .16 

13 .17 

01/31/2013 13,29 

NOx Mass 

Ib/hr 

0 - 100 

6.96 

6.95 

6.94 

6.93 

6.94 

6 . 93 

6.93 

6.07 

6.95 

6 . 92 

6.95 

6.94 

6.93 

6.93 

6.95 

6 . 95 

6.96 

6.98 

6.99 

6.98 

7.00 

6.99 

7.01 

7.00 

6.98 

6.99 

6.99 

7.01 

7.00 

7.00 

6.99 

6.11 

6.98 

6.97 

6.98 

6.96 

6.97 

6.96 

6.07 

6.92 

StkFlow 

ksefh 

0 -300000 

20489 

20450 

20449 

20447 

20483 

20463 

20463 

20465 

20486 

20432 

20503 

20496 

20438 

20445 

20458 

20487 

20518 

20532 

20578 

20548 

20594 

20548 

20608 

20565 

20556 

20554 

20535 

20575 

20538 

20557 

20545 

20538 

20510 

20510 

20508 

20502 

20488 

20486 

20397 

20384 

G12-C3 GI2-C13 G12 - CI0 G12-C6 G12-C7 G12-C8 G12 - C18 G12-C 

2>Stk CO 2>CO Mass 2>NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2 >NH3 Inj 2 >MW La 

stk co 

ppm 

0 - 1000 

3.8 

3 . 8 

3 . 8 

3.9 

3.7 

3.8 

4.0 

4.0 

3.9 

3.8 

4 . 0 

4.0 

3.9 

3.9 

3.7 

3.7 

3.7 

3.7 

3.4 

3.2 

3.6 

3.6 

3.6 

3.7 

3.5 

3.4 

3.5 

3.4 

3.5 

3.5 

3.4 

3.6 

3.6 

3.6 

3.6 

3.6 

3.3 

3.1 

2.8 

2.4 

CO Mass 

Ib/hr 

0- 100 

6.09 

6.08 

6.07 

6.06 

5.21 

6.07 

6.07 

6.07 

6.08 

6 . 06 

6.08 

6.08 

6.07 

6 . 06 

5.21 

5.21 

5.22 

5.23 

5.24 

4 . 36 

5.25 

5.24 

5.26 

5.25 

5.24 

5.24 

5.25 

5.26 

5.2S 

5.25 

5.24 

5.24 

5.23 

5.23 

5.23 

5.22 

5.23 

4.35 

4.34 

3.46 

NOx Rate 

lb/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

Stk NOXe 

ppm 

0-300 

2.21 

2.06 

2.06 

2.07 

2.14 

2.07 

2.07 

1. 99 

2.06 

2.07 

2.14 

2.14 

2.06 

2.07 

2.06 

2.06 

2.14 

2.06 

2 . 14 

2.06 

2.06 

2.06 

2.06 

2.06 

2.06 

2.13 

2.13 

2.13 

2.05 

2.13 

2.06 

1. 98 

2.06 

2.06 

2.06 

2.06 

2.06 

2.06 

1. 98 

2.06 

Stk COe Gas hsefh 

hsefh 

0 - 10000 

ppm 

0-1000 

2.90 

2.90 

2.90 

2.98 

2.83 

2.91 

3.06 

3.06 

2.98 

2.91 

3.06 

3.06 

2 . 98 

2 . 98 

2.82 

2.83 

2.83 

2.82 

2.60 

2.44 

2.75 

2.74 

2 . 74 

2.82 

2.67 

2.59 

2.66 

2 . 59 

2.66 

2 . 66 

2.59 

2.74 

2.74 

2.75 

2.74 

2.75 

2.52 

2.37 

2.13 

1. 83 

8286.0 

8270.4 

8259.0 

8247.6 

8262.0 

8254.2 

8254.2 

8254.8 

8274.0 

8241.6 

8270.4 

8267 . 4 

8254.8 

8247.0 

8273.4 

8274.6 

8287 . 2 

8303 . 4 

8322.0 

8310.0 

8328.6 

8320.8 

8344.8 

8327.4 

8313.0 

8323.2 

8326.2 

8342.4 

8338.2 

8335.2 

8319.6 

8316.6 

8305.2 

8294.4 

8304.6 

8291.4 

8296.2 

8284 . 8 

8259.6 

8243 . 4 

NH3Inj 

Ib/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

l10.0 

110.0 

l10.0 

110.0 

110.0 

2>Summary - I-Min RATA - Cont i nued 

MW Lo 

0 - 1 

99. , 

99. : 

100.1 

99. 

100.1 

99.1 

99. ! 

99. 

99 .. 

99. : 

99. : 

99 . . 

99.: 

99 . ~ 

99 .. 

99 . . 

100 . : 

100. : 

101.: 

100. ~ 

100. : 

100. : 

100 . : 

101.: 

100. : 

100. : 

100. ! 

100. : 

100.: 

101.1 

100 . . 

100. ~ 

100. : 

99. 

100. : 

100 . ~ 

100 . . 

100. : 

100.1 

100 . : 

pagE 
Group#-Channel# 

Long Descrip. 

Short Descrip . 

Units 

Range 

01/31/2013 10:23 

01/31/2013 10:24 

01/31/2013 10:25 

01/31/2013 10:26 

01/31/2013 10:27 

01/31/2013 10:28 

01/31/2013 10:29 

01/31/2 013 10:30 

01/31/2013 10:31 

01/31/2013 10:32 

01/31/2013 10:33 

01/31/2013 10:34 

01/31/2013 10:35 

01/31/2013 10:36 

01/31 /2013 10:37 

01/31/2013 10:38 

01/31/2013 10:39 

01/31/2013 10:40 

01/31/2013 10:41 

01/3 1 /2013 10:42 

01/31/2013 10:43 

01/31/2013 10:44 

01/31/2013 10:45 

01/31/2013 10: 46 

01/31/2013 10:47 

01/31/2013 10: 48 

01/31/2013 10:49 

01/31/2013 10:50 

01/31/2013 10:51 

01/31/2013 10:52 

01/31/2013 10:53 

01/3 1/2013 10:54 

01/31/2013 10:55 

01/31/2013 10:56 

01/31/2013 10:57 

01/31/2013 10:58 

01/31/2013 10:59 

01/31/2013 11:00 

01/31/2013 11:01 

01/31/2013 11:02 

Date/Time Printed: 

G12 -C2 G12-C4 G12 -C1 1 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.7 

2.7 

2.7 

2.7 

2 .• 

2.7 

2.7 

2.6 

2.7 

2.6 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.6 

2.6 

2.7 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.7 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.6 

Stk 02 

• 

0-25 

13 .17 

13 .16 

13 .17 

13 .17 

13 .17 

13 .18 

13 .17 

13 . 18 

13 .18 

13 .19 

13 .17 

13 .18 

13 .18 

13 . 18 

13 . 1 8 

13 .18 

13.17 

13 .18 

13 .17 

13 .18 

13.19 

13 .19 

13 .18 

13 . 18 

13 .18 

13 .18 

13 .19 

13 .18 

13 .17 

13 .17 

13 .17 

13 .17 

13 .17 

13 .18 

13 .17 

13 .19 

13 .18 

13 .16 

13.18 

13 . 19 

01/31/2013 13,29 

NOx Mass 

lb/hr 

0 - 100 

6.91 

6.92 

6.91 

6.92 

6.93 

6.92 

6 .9 4 

6.04 

6.93 

6.05 

6.06 

6.04 

6.91 

6.04 

6.03 

6.90 

6.05 

6.91 

6.91 

6 . 03 

6.88 

6.03 

6.04 

6.90 

6.03 

6.03 

6.03 

6.05 

6.92 

6.06 

6.05 

6.92 

6.91 

6.91 

6.92 

6.02 

6.91 

6.91 

6.03 

6.01 

G12-C20 

2>StkFlow 

StkFlow 

kscfh 

0 - 300000 

20352 

20337 

20351 

20363 

20407 

20 404 

20436 

20361 

20419 

20393 

20381 

20354 

20361 

20359 

20297 

20349 

20345 

20357 

20341 

20327 

20309 

20350 

20351 

20348 

20306 

20309 

20332 

20365 

20382 

20373 

20358 

20372 

20348 

20355 

20360 

20309 

20362 

20317 

20313 

20279 

G12-C3 

2>Stk CO 

Stk co 

ppm 

0-1000 

2.3 

2.1 

2.1 

2.0 

1.9 

1.6 

1.6 

1.5 

1.. 

1.5 

1 4 

1.4 

1.2 

1 4 

1 . 3 

1.5 

1.6 

1.3 

1.1 

1.4 

1.7 

1.8 

2.6 

3.0 

3.1 

3.2 

3.2 

3.3 

2 .• 

2.9 

2 .• 

2.9 

2.6 

2 .• 

2.9 

3.0 

3.1 

2.9 

2.8 

2 .• 

G12 - C13 GI2 -CIO G12-C6 

2>CO Mass 2>NDx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

3.46 

3.46 

3.46 

2.59 

2.60 

2.60 

2.60 

2.59 

2.60 

2. 59 

1. 73 

1. 73 

1. 73 

1. 73 

1. 72 

2.59 

2.59 

1. 73 

1. 73 

1. 72 

2.58 

2.59 

3.45 

4.31 

4.31 

4.31 

4.31 

5.18 

4.33 

4.33 

4.32 

4.33 

3.46 

4.32 

4.32 

4.30 

4.32 

4.32 

4.3 1 

4.29 

NDx Rate 

Ib/mmBtu 

0-1 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.008 

0.007 

0.008 

0.008 

0.007 

0.008 

0.007 

0.007 

0 . 008 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.007 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

2.06 

2.06 

2.06 

2.06 

2.14 

2.06 

2.06 

1. 99 

2.06 

1. 99 

1. 98 

1. 99 

2.06 

1. 99 

1. 99 

2.06 

1. 98 

2.06 

2.06 

1. 99 

2.07 

1. 99 

1. 99 

2.06 

1. 99 

1. 99 

1. 99 

1. 99 

2.06 

1. 98 

1. 98 

2.06 

2.06 

2.06 

2.06 

1. 99 

2.06 

2.06 

1. 99 

1. 99 

G12-C7 GI2 -C8 

2>Stk CDc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

1. 76 

1.60 

1. 60 

1. 53 

1.45 

1.22 

1.22 

1.15 

1.38 

1.15 

1. 07 

1. 07 

0.92 

1. 07 

0.99 

1.15 

1. 22 

0.99 

0.84 

1. 07 

1.30 

1. 38 

1. 99 

2.29 

2.37 

2.45 

2.45 

2.52 

2.14 

2.21 

2.14 

2.21 

1. 98 

2.14 

2.21 

2 . 30 

2.37 

2.21 

2.14 

2.14 

8230.8 

8235.0 

8230.2 

8235.0 

8253.0 

8241.0 

8264.4 

8223.6 

8247.0 

8226.0 

8242.2 

8220 . 6 

8223.6 

8223.0 

8197.8 

8218.8 

8227.8 

8221.8 

8226.0 

8209.8 

8191.8 

8208.6 

8219.4 

8218.2 

8201.4 

8202.6 

8201.4 

8225.4 

8242.8 

8239.2 

8233.2 

8238.6 

8229.0 

8221.2 

8233.8 

8191.8 

8224.2 

8227.2 

8204.4 

8179.8 

GI2-C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110 .0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - 1-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

100. : 

99 . . 

99. 

100 . 

100.: 

100 .. 

100 .. 

99. 

100. : 

100.: 

100.1 

99. ~ 

99 .. 

100.: 

99.: 

99. ~ 

99 . ~ 

99 .. 

100 . 

99. 

99 . . 

99 .. 

99. : 

99. ! 

99 .. 

99 .. 

99.: 

99 . . 

100 . . 

99.: 

99 . . 

100.: 

100 .1 

100. 

100.1 

99. 

99. 

9 9. ! 

99 .. 

99. 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descrip. 

Units 

Range 

01/31/2013 11;03 

01/31/2013 11;04 

01/31/2013 11;05 

01/31/2013 11;06 

01/31/2013 11;07 

01/31/2013 11;08 

01/31/2013 11;09 

01/31/2013 11;10 

01/31/2013 11;11 

01/31/2013 11;12 

01/31/2013 11;13 

01/31/2013 11;14 

01/31/2013 11;15 

01/31/2013 11;16 

01/31/2013 11;17 

01/31/2013 11;18 

01/31/2013 11;19 

01/31/2013 11;20 

01/31/2013 11:21 

01/31/2013 11:22 

01/31/2013 11:23 

01/31/2013 11:24 

01/31/2013 11;25 

01/31/2013 11;26 

01/31/2013 11:27 

01/31/2013 11:28 

01/31/2013 11:29 

01/31/2013 11:30 

01/31/2013 11:31 

01/31/2013 11:32 

01/31/2013 11:33 

01/31/2013 11:34 

01/31/2013 11:35 

01/31/2013 11;36 

01/31/2013 11:37 

01/31/2013 11:38 

01/31/2013 11:39 

01/31/2013 11:40 

01/31/2013 11:41 

01/31/2013 11:42 

Date/Time Printed: 

G12-C2 G12-C4 G12-Cll 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.6 

2.6 

2.6 

2.7 

2.7 

2.8 

2.7 

2.7 

2.7 

2.6 

2.8 

2.7 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.8 

2.7 

2.7 

2.6 

2.8 

2.6 

2.8 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.6 

2.6 

2.7 

2.7 

2.7 

2.7 

2.7 

2.5 

2.6 

Stk 02 

• 

0-25 

13 .19 

13 .19 

13 .18 

13 .17 

13 .16 

13 .15 

13 .16 

13 .16 

13 .16 

13 .16 

13 .15 

13 . 15 

13 .16 

13 .17 

13 .18 

13 .18 

13 .17 

13 .18 

13 .18 

13 .17 

13 .16 

13 .16 

13 . 15 

13 .16 

13 .16 

13 .18 

13 .16 

13 .17 

13 .15 

13 .15 

13 .17 

13 .17 

13 .17 

13 .16 

13 . 15 

13 . 15 

13 .16 

13 .15 

13 .17 

13 .16 

01/31/2013 13,29 

NOx Mass 

Ib/hr 

0-100 

6.02 

6.03 

6.03 

6.91 

6.93 

6.94 

6.92 

6.94 

6.91 

6.04 

6.93 

6.92 

6.92 

6.92 

6.91 

6.04 

6.91 

6.04 

6.90 

6.92 

6.93 

6.06 

6 . 94 

6.05 

6.92 

6.04 

6.93 

6.05 

6.93 

6.94 

6.05 

6.05 

6.04 

6.92 

6.93 

6.92 

6.91 

6.93 

6.04 

6.04 

G12 -C20 

2>StkFlow 

StkFlow 

kscfh 

0-300000 

20291 

20323 

20297 

20348 

20368 

20365 

20359 

20397 

20320 

20307 

20340 

20318 

20342 

20357 

20377 

20330 

20332 

20337 

20343 

20367 

20363 

20347 

20392 

20334 

20334 

20337 

20365 

20342 

20338 

20389 

20339 

20341 

20332 

20331 

20341 

20303 

20307 

20343 

20314 

20310 

G12-C3 

2>Stk CO 

Stk co 

ppm 

0-1000 

2.8 

2.9 

2.' 

2.9 

2.9 

3.2 

2.7 

2.8 

2.8 

2.9 

2.9 

2.7 

2.6 

2.' 

3.1 

3.0 

2.' 

3.1 

3.0 

2.9 

2.9 

3.1 

3.1 

2.9 

3.2 

3.3 

3.1 

3.4 

3.1 

3.3 

3.2 

3.2 

3.5 

3.5 

3 .4 

3.4 

3.2 

3.3 

3.4 

3.2 

G12-C13 G12 -ClO G12-C6 

2>CO Mass 2>NOx Rate 2>Stk NOXc 

CO Mass 

Ib/hr 

0-100 

4.30 

4.30 

4.30 

4.32 

4.33 

4.34 

4.33 

4.34 

4.32 

4.32 

4.33 

4.33 

3.46 

4.32 

4.32 

4.31 

4.32 

4.31 

4.31 

4.32 

4.33 

4.33 

4. 34 

4.32 

4.32 

5.18 

4.33 

5.18 

4.33 

5.21 

4.32 

4.32 

5.18 

5.19 

5.20 

5.19 

4.32 

5.20 

5.18 

4.32 

NOx Rate 

Ib/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0.007 

0.008 

0.007 

0.008 

0.008 

0.007 

0.007 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.007 

Stk NOXc 

ppm 

0-300 

1. 99 

1. 99 

1. 99 

2.06 

2.06 

2.13 

2.06 

2.06 

2.06 

1. 98 

2.13 

2.06 

2.06 

2.06 

2.06 

1. 99 

2.06 

1. 99 

2.14 

2.06 

2.06 

1. 98 

2.13 

1. 98 

2.13 

1. 99 

2.06 

1. 98 

2.06 

2.06 

1. 98 

1. 98 

1. 98 

2.06 

2.06 

2.06 

2.06 

2.06 

1. 91 

1. 98 

G12-C7 G12-C8 

2>Stk COc 2>Gas Flow 

Stk COc Gas hscfh 

ppm hscfh 

0-1000 0-10000 

2.14 

2.22 

2.22 

2.21 

2.21 

2.44 

2.06 

2.13 

2.13 

2.21 

2.21 

2 .06 

1. 98 

2.21 

2.37 

2.29 

2 .21 

2.37 

2.29 

2.21 

2.21 

2.36 

2.36 

2.21 

2.44 

2.52 

2.36 

2.60 

2.36 

2.51 

2.44 

2.44 

2.67 

2.67 

2.59 

2.59 

2.44 

2.51 

2.60 

2.44 

8184.6 

8197.8 

8197.8 

8229.0 

8247.6 

8257.2 

8244. a 

8259.6 

8228.4 

8223.0 

8247.0 

8238.0 

8237.4 

8232.6 

8230.2 

8211.0 

8222.4 

8214.0 

8216.4 

8236.8 

8245.8 

8239.2 

8268.0 

8233.8 

8233.8 

8214.0 

8246.4 

8226.6 

8246.4 

8266.8 

8225.4 

8226.0 

8222.4 

8232.6 

8247.6 

8232.0 

8223.0 

8248.2 

8215.2 

8224.2 

G12 -C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2>Summary - 1-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

99. c 

99.: 

99.: 

100.1 

100. 

100. 

100. 

100 .. 

100. ( 

99. 

100. : 

99. ; 

9 •. 

99. 

1 00.1 

1 00. r 

99.! 

99 .. 

99 .. 

100 .. 

100, . 

99, ' 

100. ' 

99, ' 

99, ; 

99. ! 

100. : 

100,1 

100.1 

101,1 

100 . . 

99. 

99, ' 

99. ' 

100. 

99, ! 

99.' 

100.1 

99 . 

100." 

PagE 
Group#-Channel# 

Long Descrip . 

Short Descrip . 

Units 

Range 

01/31/2013 11;43 

01/31/2013 11 . 44 

01/31/2013 11:45 

01/31/2013 11;46 

01/31/2013 11;47 

01/31/2013 11:48 

01/31/ 2 013 11:49 

01/31/ 2 013 11:50 

01/31/ 2 013 11:51 

01/31/2013 11:52 

01/31/2013 11:53 

01/31/2013 11:54 

01/31/2013 11:55 

01/31/2013 1 1 :56 

01/31/2013 11:57 

01/31/2013 11:58 

01/31/2013 11:59 

01/31/ 2 013 12:00 

01/31/2013 12:01 

01/31/2013 12:02 

01/31/2013 12:03 

01/31/2013 12:04 

01/31/ 2 013 1 2 : 05 

01/31/2013 12:06 

01/31/2013 12:07 

01/31/2013 12:08 

01/31/2013 12:09 

01/31/2013 12:10 

01/31/2013 12:11 

01/31/2013 12:12 

01/31/2013 12:13 

01/31/2013 12:14 

01/31/2013 12:15 

01/31/2013 12:16 

01/31/ 2 013 12:17 

01/31/2013 12:18 

01/31/2 013 12:19 

01/31/ 2 013 12:20 

01/31/ 2 013 12:21 

01/31/2013 12:22 

Date/Time Printed: 

G12 - C2 G12-C4 G12 -Cl1 

2>Stk NOx 

Stk NOx 

ppm 

0-150 

2>Stk 02 2>NOx Mass 

2.6 

2.6 

2.6 

2.6 

2.7 

2.6 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.7 

2.7 

2.7 

2.6 

2.6 

2.7 

2.6 

2.6 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.6 

2.7 

2.6 

2.6 

2.7 

Stk 02 

• 

0-25 

13 .17 

13 .17 

13 . 17 

13 .16 

13 .15 

13 . 14 

13 . 14 

13 . 14 

13 . 13 

13 . 13 

13 . 13 

13 .14 

13 .14 

13 .15 

13 .13 

13 .13 

13 .13 

13 .13 

13 . 13 

13 . 11 

13 .11 

13 .12 

13 . 13 

13 . 14 

13 . 13 

13 .14 

13 .14 

13 .14 

13 . 15 

13.14 

13 .13 

13.14 

13.13 

13.14 

13 .13 

13 . 14 

13 .14 

13 .15 

13 .14 

13 . 14 

01/31/2013 13,29 

NOx Mass 

1b/hr 

0-100 

6.03 

6.03 

6.04 

6.04 

6.92 

6.06 

6.93 

6.93 

6.94 

6.94 

6.95 

6.95 

6.92 

6.05 

6.94 

6.06 

6.93 

6.93 

6.07 

6.96 

6.96 

6.95 

6.94 

6.06 

6.06 

6.92 

6.06 

6.05 

6.91 

6.91 

6.91 

6.03 

6.92 

6.04 

6.92 

6.04 

6.90 

6.02 

6.02 

6.89 

G12-C20 

2 >StkFlow 

StkFlow 

ksefh 

0-300000 

20292 

20298 

20324 

20283 

20327 

20296 

20317 

20320 

20317 

20326 

20344 

20376 

20306 

20312 

20317 

20298 

20308 

20301 

20302 

20324 

20325 

20322 

20310 

20312 

20286 

20289 

20297 

20265 

20279 

20262 

20249 

20210 

20259 

20238 

20258 

20240 

20221 

20216 

20182 

20218 

G12-C3 

2>Stk CO 

Stk co 

ppm 

0-1000 

3.6 

3.3 

3.3 

3.2 

3.3 

3 . 4 

3.4 

3.1 

3 . 1 

3.0 

3 . 3 

3.2 

3.2 

3.4 

3.4 

3.1 

3.1 

3.1 

3.0 

2.8 

3.3 

3.1 

2.9 

2.9 

3 . 1 

3.1 

3.2 

3.2 

3.4 

3.3 

3 . 4 

3.5 

3.2 

3.2 

2.7 

3.1 

3.0 

2.8 

3.0 

3.1 

GI2 - C13 G12-C10 G12-C6 

2>CO Mass 2 >NOx Rate 2>Stk NOXe 

CO Mass 

lb/hr 

0-100 

5.17 

5.17 

5.18 

4.31 

5.19 

5.19 

5.20 

4.33 

4 . 34 

4.34 

5.21 

4.34 

4.33 

5.19 

5.20 

4.33 

4.33 

4.33 

4.33 

4 . 35 

5.22 

4 . 3 4 

4 .33 

4 .33 

4.33 

4.32 

4.33 

4.32 

5.18 

5.18 

5.19 

5.17 

4.32 

4.31 

4.32 

4.31 

4. 31 

4.30 

4 . 30 

4 .31 

NOx Rate 

lb/mmBtu 

0-1 

0.007 

0.007 

0.007 

0.007 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0.008 

0.007 

0.008 

0.008 

0.008 

0.008 

0 . 007 

0.007 

0.008 

0.007 

0.007 

0.008 

0.008 

0.008 

0.007 

0.008 

0.007 

0.008 

0.007 

0.008 

0.007 

0.007 

0.008 

Stk NOXe 

ppm 

0-300 

1. 98 

1. 98 

1. 98 

1. 98 

2.06 

1. 98 

2 . 05 

2.05 

2.05 

2.05 

2.05 

2.05 

2.05 

1. 98 

2.05 

1. 97 

2.05 

2.05 

1. 97 

2.04 

2.04 

2 . 05 

2.05 

1 . 98 

1. 97 

2.05 

1. 98 

1. 98 

2.06 

2.05 

2.05 

l. 98 

2.05 

1. 98 

2.05 

1. 98 

2.05 

1. 98 

1. 98 

2.05 

G12-C7 G12-C8 

2>Stk COe 2>Gas Flow 

Stk COe Gas hsefh 

ppm hscfh 

0-1000 0-10000 

2.75 

2.52 

2 . 52 

2.44 

2.51 

2 . 59 

2.59 

2. 3 6 

2.35 

2.28 

2 . 51 

2 .4 3 

2.43 

2.59 

2.58 

2.35 

2.35 

2.35 

2.28 

2.12 

2.50 

2 .35 

2 .20 

2 .2 0 

2 . 35 

2.36 

2.43 

2.43 

2.59 

2.51 

2.58 

2 . 66 

2.43 

2 . 43 

2.05 

2.36 

2 .28 

2.13 

2 . 2 8 

2.36 

8206.2 

8208 . 6 

8219.4 

8213.4 

8241.6 

8239 . 8 

8248.2 

8249.4 

8259.0 

8262.6 

8269.8 

8272.2 

8244.0 

8235.6 

8259.0 

8251.2 

8255.4 

8252.4 

8253.0 

8283.0 

8283.6 

8271.6 

8256.0 

824 6.4 

8246.4 

8236.8 

8240.4 

8227.2 

8222.4 

8226.0 

8231.4 

8205.0 

8235.6 

8216.4 

8235.0 

8217.0 

8209.2 

8196.6 

8193.6 

8208.0 

G12 -C18 

2>NH3 Inj 

NH3Inj 

1b/hr 

0-1000 

110.0 

llO.O 

110.0 

110.0 

110.0 

110.0 

110 . 0 

1 1 0.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

1 1 0.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110 . 0 

110 . 0 

110.0 

110.0 

110.0 

2>Summary - I-Min RATA - Continued 

G12-C 

2>MW Lo 

MW Lo 

0-1 

99 . ! 

99.: 

99 . . 

100.1 

100.1 

100 . : 

100. : 

100 . : 

100 . 

100 . . 

100. 

100. 

99. 

99 . . 

99. 

100. 

100. 

100. ! 

100.: 

100 . . 

100 .. 

100. : 

100. ! 

100. ( 

100 . : 

100. ( 

100. 1 

99 . . 

100.1 

100. : 

100 . . 

99 . . 

99 .. 

99. 

99. 

99 .. 

99 . . 

99 .. 

98. 

99 .. 

pagE 
Group#-Channel# 

Long Descrip . 

Sho r t Descrip . 

Units 

Range 

01/31/2013 12:23 

01/31/2013 12:24 

01/31/2013 12:25 

01/31/2013 12:26 

01/31/2013 12:27 

01/31/2013 12:28 

01/31/2013 12:29 

01/31/2013 12:30 

01/31/2013 12:31 

01/31/2013 12:32 

01/31/2013 12:33 

01/31/2013 12:34 

01/31/2013 12:35 

01/31/2013 12:36 

01/ 31/2013 12:37 

01/31/2013 12:38 

01/31/2013 12:39 

Perio d Ave rage 

Period Max Value 

Pe rio d Min Value 

Period Totals = 

Period % Recovery 

Date/Time Printed: 

G12 - C2 G12-C4 G12 - C11 G12 - C20 

2>Stk NOx 

Stk NOx 

ppm 

0 - 150 

2>Stk 02 2>NOx Mass 2>StkF!ow 

2.7 

2.7 

2.8 

2.7 

2.7 

2.6 

2.7 

2.7 

2.6 

2.7 

2.8 

2.7 

2.7 

2.7 

2.6 

2.7 

2.6 

2.7 

2.9 

2.5 

6.6540E+2 

100.0 

Stk 02 

• 

0-25 

13.13 

13 .13 

13.10 

13 .11 

13 .10 

13 . 11 

13 .10 

13 .12 

13 .11 

13 .11 

13 .10 

13 .12 

13 .11 

13 .13 

13 .11 

13 .12 

13 .11 

13 .17 

13.21 

13 .10 

3.2518E+3 

100 . 0 

01/31/2013 13,29 

NOx Mass 

1b/ hr 

0 - 100 

6.93 

6.92 

6.94 

6.94 

6.94 

6.07 

6.93 

6.92 

6.06 

6.92 

6.94 

6.93 

6.92 

6.92 

6.05 

6.90 

6.05 

6.72 

7.06 

6.01 

1.6602E+3 

100.0 

StkFlow 

ksefh 

0-300000 

20283 

202 57 

20261 

20268 

20246 

20249 

20212 

20241 

20216 

20213 

20232 

20267 

20227 

20254 

20193 

20189 

20203 

20411 

20716 

20182 

5.0416E+6 

100.0 

G12-C3 G12 -Cl3 G12 - C10 G12 -C6 G12-C7 G12 - C8 G12 - C18 G12-C 

2>Stk CO 2>CO Mass 2 >NOx Rate 2>Stk NOXe 2>Stk COe 2>Gas Flow 2>NH3 Inj 2>MW La 

Stk CO 

ppm 

0-1000 

3.0 

2.9 

2.8 

2.8 

3.0 

3.0 

2.9 

2.7 

3.0 

3.3 

3.0 

2.9 

3.0 

2.6 

3.2 

3.1 

3.1 

3.0 

4.0 

1.1 

7.3600E+2 

100.0 

CO Mass 

1b/ hr 

0-100 

4.33 

4.32 

4.34 

4.34 

4.34 

4.33 

4 . 33 

4.33 

4.33 

5.19 

4.33 

4.33 

4.33 

3.46 

4.32 

4.31 

4.32 

4.41 

6.09 

1. 72 

1 . 0895E+3 

100.0 

NOx Rate 

Ib/mmBtu 

0-1 

0.008 

0. 0 08 

O.OOB 

O.OOB 

O.OOB 

0.007 

O.OOB 

O.OOB 

0.007 

O.OOB 

O.OOB 

0.008 

O.OOB 

0.008 

0.007 

0.008 

0.007 

O.OOB 

0.008 

0.007 

1.9139E+0 

100.0 

Stk NOXe 

ppm 

0-300 

2.05 

2.05 

2.12 

2.04 

2.04 

1. 97 

2.04 

2.05 

1. 97 

2.04 

2.12 

2.05 

2.04 

2.05 

1. 97 

2.05 

1. 97 

2.05 

2.21 

1. 91 

5.0755E+2 

100.0 

Stk COe Gas hsefh 

ppm hsefh 

0-1000 0-10000 

2.28 

2.20 

2.12 

2.12 

2.27 

2.27 

2 . 19 

2.05 

2.27 

2.50 

2.27 

2.20 

2.27 

1. 97 

2.42 

2.35 

2.35 

2.27 

3.06 

0.84 

5.6129E+2 

100.0 

8245.2 

8234.4 

8268.0 

8260.2 

8262.0 

8252.4 

8248.2 

8238.6 

8239.2 

8238.0 

8256.0 

8249.4 

8243.4 

8233.2 

8229.6 

8217.6 

8233.8 

8259.7 

8410.2 

8179.8 

2.0401E+6 

100.0 

NH3Inj 

1b/hr 

0 - 1000 

110.0 

110 . 0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

110.0 

2.7170E+4 

100.0 

2>Summary - 1-Min RATA - Continued 

MW Lo 

0-1 

100. 

100. -

100. : 

100. : 

100. : 

100. 

100. ( 

100 . ( 

100. ( 

100. ( 

100.: 

100 .. 

99. 

100. : 

99 .. 

99. : 

99 . . 

100.0 

101. 

98. 

2.4714E+· 

100. 

pagE 
Appendix B.2 Fuel Analysis Data 

R0410673 B-6 
Saybolt 

A COli( U URAlDIlJ[S (8ttPAMY 

SAYBOLTLP 

21730 S. Wilmington Avenue 

Suite 201 

Carson, CA 90810 

3 10-518-4400 Telephone 

310-518-4455 Facsimile 

Fast To The Point 

Saybolt LP 

Certificate of Analysis 

DELTA AIR QUALITY SERVICES 

BOB FINKEN 

1845 N. CASE 

ORANGE, CA 92865 

Report Date: 2/6/2013 

Job No: 13091-00008592 

Sample Number: 1300103-03 

Client Ref: Gemma 

Test 

Refinery Gas Analysis 

Hydrogen 

Carbon Dioxide 

Carbon Monoxide 

Nitrogen 

Oxygen 

Methane 

Ethylene 

Ethane 

Propane 

Propylene 

Isobutane 

n-Butane 

1-Butene 

Isobutylene 

t-2-Butene 

c-2-Butene 

1,3-Butadiene 

Isopentane 

n-Pentane 

Hexanes Plus 

Total 

Molar Mass Ratio 

Relative Density 

Compressability Factor 

Gross Heating Value (Dry-Ideal) 

Gross Heating Value (Dry-Real) 

Gross Heating Value (Wet-Ideal) 

Net Heating Value (Dry-Ideal) 

Method 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

Date Sampled: 2/1/2013 

Product: Natural Gas 

Location: NG line - 2 

Sample 10: Test #S2/NG line-Fuel Sulfur-1 

Vessel: 

Result Units 

<0.001 mole% 

0.538 mole% 

<0.001 mole% 

4.778 mole% 

0.037 mole% 

89.675 mole% 

<0.001 mole% 

4.360 mole% 

0.480 mole% 

<0.001 mole% 

0.034 mole% 

0.057 mole% 

<0.001 mole% 

<0.001 mole% 

<0.001 mole% 

<0.001 mole% 

<0.001 mole% 

0.012 mole% 

0.009 mole% 

0.020 mole% 

100.000 mole% 

0.60710 

0.60927 

0.996 

1000 BTU/cf 

1004 BTU/cf 

983 BTU/cf 

900 BTU/cf 

isslier warrants that II has e~er~ised due diligence and care with respc<:l to the infonnal;on and professIOnal Jl>dgments embodied In this .epan. This repa" renCCts only the findings al the lime and place of inspection 

and lestlnS. Iss~r cKpressly disclaims 111)1 further indemnity of any k.llld. This feJl(lrt is nol. guarlr'llee or polley ofmsuran ce WIth respect to the goods or the conlracwal performance of any party Any perwn relYing 

upon Ihls ,epon should be aware that issuer's activities are carried 0111 under their lIeneral terms and oonditions. 

"PrCClsion parameters apply In the evaluation of the test results specified above. Please also refer to ASTM 03244 (ex~pt for analysis of RFG) and I? 367 with respect to the ulIlluuion of the test data to deteflTllne 

conformance with specifications," 

Page 7 of 12 
SAYBOLTLP 

21730 S. Wilmington Avenue 

Suite 20 I 

Fast To The Point 

5aybolt: 

Carson, CA 90810 

310-518-4400 Telephone 

3 10-518-4455 Facsimile A [ORt l"BORATOIIJ[S CO I1 P"'1Y 

OEL TA AIR OUALITY SERVICES 

BOB FINKEN 

1845 N. CASE 

ORANGE, CA 92865 

Report Oate: 2/6/2013 

Job No: 13091-00008592 

Sample Number: 1300103-03 

Client Ref: Gemma 

Test 

Refinery Gas Analysis 

Pressure Base 

Ethylene 

Ethane 

Propane 

Propylene 

Isobutane 

n-Butane 

1-Butene 

Isobutylene 

t-2-Butene 

c-2-Butene 

1,3-Butadiene 

Isopentane 

n-Pentane 

Hexanes Plus 

Total 

Carbon 

Hydrogen 

Nitrogen 

Oxygen 

Gross Heating Value 

Fuel Factor (FD) 

Average Molecular Weight 

Sulfur Speciation 

Hydrogen SUlfide 

Carbonyl SUlfide 

SUlfur Oioxide 

Methyl Mercaptan 

Certificate of Analysis 

Oate Sampled: 

Product: 

Location: 

Sample 10: 

Vessel: 

Method Result 

ASTM 0-3588 14.696 

ASTM 0-3588 <0.001 

ASTM 0-3588 1.163 

ASTM 0-3588 0.132 

ASTM 0-3588 <0.001 

ASTM 0-3588 0.011 

ASTM 0-3588 0.Q18 

ASTM 0-3588 <0.001 

ASTM 0-3588 <0.001 

ASTM 0-3588 <0.001 

ASTM 0-3588 <0.001 

ASTM 0-3588 <0.001 

ASTM 0-3588 0.004 

ASTM 0-3588 0.003 

ASTM 0-3588 0.008 

ASTM 0-3588 1.339 

ASTM 0-3588 68.986 

ASTM 0-3588 22.353 

ASTM 0-3588 7.614 

ASTM 0-3588 1.047 

ASTM 0-3588 21192 

ASTM 0-3588 8847 

ASTM 0-3588 17.58 

AOMO 307/ASTM 05504 <0.1 

AOMO 307/ASTM 05504 <0.1 

AOMO 307/ASTM 05504 <0.1 

AOMO 307/ASTM 05504 <0.1 

Saybolt LP 

2/1/2013 

Natural Gas 

NG Line - 2 

Test #S2/NG Line-Fuel SUlfur-1 

Units 

psi 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

GPM 

wt% 

wt% 

wt% 

wt% 

BTU/lb 

SCF/mm BTU 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

issuer warnnlS IMI il has exerdsed due diligence and care with respect to the II'I o~tion and professional judgments embodied in this report. This report reflects only me findings althe time and place of inliJH:CtHlII 

and testing. Issuer elCpfes$ly dIsclaims any further indemnity or any kind. This report is not l guarantee or policy of insurance ""th respect to the good$ or the canltlCllla! performance of any party Any person rdying 

upon this report should be aware that ,ssuets activities are earned ()UI WIder their genaallemtS and conditions. 

"Precision parameters apply in the evaluatiOn of the test rcsults 5ptcified abo~ . Please also refer to ASTM 03244 (except for analysis ofRFG) and IF 361 with respect to the utilization of the test dati to determine 

conformance with specifications," 

Page 8 of 12 
SAYBOLTLP 

21730 S. Wilmington Avenue 

Suite 201 

Fast To The Point 

5iJyboit 

II CO il E tAB DIIATClIlES COMPANY 

Carson, CA 90810 

310-518-4400 Telephone 

310-518-4455 Facsimile 

Certificate of Analysis 

DELTA AIR QUALITY SERVICES 

BOB FINKEN 

1845 N. CASE 

ORANGE, CA 92865 

Saybolt LP 

Date Sampled: 2/1/2013 

Report Date: 2/6/2013 

Job No: 13091-00008592 

Sample Number: 1300103-03 

Client Ref: Gemma 

Test 

Sulfur Speciation 

Ethyl Mercaptan 

Dimethyl Sulfide 

Carbon Disulfide 

2-Propanethiol 

tert-Butyl Mercaptan 

1-Propanethiol 

Thiophene 

Diethyl Sulfide 

n-Butyl Mercaptan 

Dimethyl Disulfide 

tetra-Hydro Thiophene 

n-Pentanethiol 

Diethyl Disulfide 

Total Unknown Mercaptan 

Total Reduced Sulfur 

Product: 

Location: 

Sample ID: 

Vessel: 

Method Result 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AOMD 307/ASTM D5504 <0.1 

AOMD 307/ASTM D5504 <0.1 

AOMD 307/ASTM D5504 <0.1 

AOMD 307/ASTM 05504 <0.1 

AOMO 307/ASTM D5504 <0.1 

AOMO 307/ASTM 05504 <0.1 

AOMO 307/ASTM 05504 <0.1 

AOMD 307/ASTM 05504 <0.1 

AOMO 307/ASTM 05504 0.2 

AOMO 307/ASTM 05504 0.2 

Approved By: 

Natural Gas 

NG Line - 2 

Test #S2ING Line-Fuel Sulfur-1 

Units 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

ppm v/v 

Signature On File 

Francine Hanby 

Laboratory Manager 

Issuer warrants thai il has exercised due dlhgence and care with respecllO the Inform.hOlland professional judgments embodied in this . epo<t. TIuS~!1 .efleets only the findings aI the time Uld place oftn!ip«!ion 

and testing. Issuer ClqIressly dl$CiaJn1$ any further llldemnily of any kind. Th,s .eporl is 1101 a guarant~ Or policy of illsurance WIth respect to rhe goods or the contraClual perfofTTW1ce arany party. Any person relying 

upon this .epon should be .ware that I$SUO::r'S a<;:bVlties Me earned out \II1der their general terms and conditions. 

"Preeision parameters apply in the evillualiOll of tile lest results specifIed .wove. Please also refer to ASTM 03244 (exUPI for analysis of RFG) and IP 367 WIth respect to the utiliution of the leSI dal. 10 determi~ 

tonfonnance with specifications." 

Page 9 of 12 
Say bolt: A (01£ LAIOR"TDJlU:S CG J'lPANJ 

SAYBOLTLP 

21730 S. Wilmington Avenue 

Suite 201 

Carson, CA 90810 

310-518-4400 Telephone 

310-518-4455 Facsimile 

Fast To The Point 

Saybolt LP 

Certificate of Analysis 

DELTA AIR QUALITY SERVICES 

BOB FINKEN 

1845 N. CASE 

ORANGE, CA 92865 

Report Date: 

Job No: 

Sample Number: 

Client Ref: 

Test 

2/6/2013 

13091-00008592 

1300103-04 

Gemma 

Refinery Gas Analysis 

Hydrogen 

Carbon Dioxide 

Carbon Monoxide 

Nitrogen 

Oxygen 

Methane 

Ethylene 

Ethane 

Propane 

Propylene 

Isobutane 

n-Butane 

1-Butene 

Isobutylene 

t-2-Butene 

c-2-Butene 

1,3-Butadiene 

Isopentane 

n-Pentane 

Hexanes Plus 

Total 

Molar Mass Ratio 

Relative Density 

Compressability Factor 

Gross Heating Value (Dry-Ideal) 

Gross Heating Value (Dry-Real) 

Gross Heating Value (Wet-Ideal) 

Net Heating Value (Dry-Ideal) 

Method 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 01945/01946 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0-3588 

ASTM 0 -3588 

ASTM 0-3588 

Date Sampled: 2/1/2013 

Product: 

Location: 

Sample 10: 

Vessel: 

Result 

<0001 

0.555 

<0.001 

2.475 

0.015 

91.836 

<0.001 

4.481 

0.494 

<0.001 

0.036 

0.058 

<0.001 

<0.001 

<0.001 

<0.001 

<0.001 

0.013 

0.014 

0.022 

99.999 

0.59853 

0.60068 

0.996 

1025 

1029 

1007 

923 

Natural Gas 

NG Line - 2 

Test #S2/NG Line-Fuel Sulfur-2 

Units 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

mole% 

BTU/cf 

BTU/cf 

BTU/cf 

BTU/cf 

Issuer warrants thaI it lias exercised due diligence and care with r~ 10 the informllion and pl"ofcssional j...ogments embodied in this report. This rcpo" renecl5 only the findings at the bmc and place ofinspeclion 

and testing. Issuer expre:;sly disclaims 8/\)1 further indemnity of My kind. nus repo!1 is noll guarantee or policy of insurance with respect to the goods or the confractual performance of any party. Any per$Oll relying 

upon this Tepo" should be aware that issuer's acrivities are carried OUI under their generillerms and conditions. 

"Precision parameters apply In the evaluation of the lest results specified above. Pl ease also refer 10 ASTM 03244 (except for analysis ofRFG) and IP 367 wlIh respecllo Ihe uulization of the le5t data to determine 

confonmance 'Him spedficllions." 

Page10of12 
SAYBOLTLP 

2 1730 S. Wilmington Avenue 

Suite 201 

Fast To The Point 

Saybolt. A CORE lA.80RAiUR[[S CDI1PAHY 

Carson, CA 90810 

310-518-4400 Telephone 

310-518-4455 Facsimile 

Certificate of Analysis 

DELTA AIR QUALITY SERVICES 

BOB FINKEN 

1845 N. CASE 

ORANGE, CA 92865 

Saybolt LP 

Date Sampled: 2/1/2013 

Report Date: 2/6/2013 

Job No: 13091-00008592 

Sample Number: 1300103-04 

Client Ref: Gemma 

Test 

Refinery Gas Analysis 

Pressure Base 

Ethylene 

Ethane 

Propane 

Propylene 

Isobutane 

n-Butane 

1-Butene 

Isobutylene 

t-2-Butene 

c-2-Butene 

1,3-Butadiene 

Isopentane 

n-Pentane 

Hexanes Plus 

Total 

Carbon 

Hydrogen 

Nitrogen 

Oxygen 

Gross Heating Value 

Fuel Factor (FO) 

Average Molecular Weight 

Sulfur Speciation 

Hydrogen Sulfide 

Carbonyl Sulfide 

Sulfur Dioxide 

Methyl Mercaptan 

Product: Natural Gas 

Location: NG Line - 2 

Sample 10: Test #S2/NG Line-Fuel Sulfur-2 

Vessel: 

Method Result Units 

ASTM 0-3588 14.696 psi 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 1.196 GPM 

ASTM 0-3588 0.136 GPM 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 0.012 GPM 

ASTM 0-3588 0.018 GPM 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 <0.001 GPM 

ASTM 0-3588 0.005 GPM 

ASTM 0-3588 0.005 GPM 

ASTM 0-3588 0.009 GPM 

ASTM 0-3588 1.381 GPM 

ASTM 0-3588 71 .719 wt% 

ASTM 0-3588 23.229 wt% 

ASTM 0-3588 4.001 wt% 

ASTM 0-3588 1.052 wt% 

ASTM 0-3588 22029 BTUllb 

ASTM 0-3588 8823 SCF/mm BTU 

ASTM 0-3588 17.34 

AQMO 307/ASTM 05504 <0.1 ppm v/v 

AQMO 307/ASTM 05504 <0.1 ppm v/v 

AQMO 307/ASTM 05504 <0.1 ppm v/v 

AQMO 307/ASTM 05504 <0.1 ppm vlv 

S5~r warrants thaI il has exerCised due dih~ce and care willi respect 10 lIle inronnalion and professional judgments embodied in this report. This repon refleets only the findings atlhe lime and place of insp«tion 

Uld testing. Issuer expressly dlsclaims .... y further indemnity of any kind. This lepan is nol a guarantee or policy o[insurance with respect \0 rhe goods or the conlractuaJ perfonnance of any part)'. Any person relying 

upon this repo" should be aware thallssue~5 activities are carried 01,11 under the,r general terms and conditions. 

"Precision parameters apply in the evall.lltion of the teSI results specified abo~. Ple..se 11150 refer to ASlM 03244 (except for analysis of RFG) and IP 367 with rcspecllO the utilization of the test dati to detennine 

conformllflGe with specificallons," 

Page 11 of 12 
SAYBOLTLP 

21730 S. Wilmington Avenue 

Suite 201 

Fast To The Point 

5aybolt 

II COM( lAURATORI£S COMPA.NY 

Carson, CA 90810 

310-518-4400 Telephone 

310-518-4455 Facsimile 

Certificate of Analysis 

DELTA AIR QUALITY SERVICES 

BOB FINKEN 

1845 N. CASE 

ORANGE, CA 92865 

Saybolt LP 

Date Sampled: 2/1/2013 

Report Date: 2/6/2013 

Job No: 13091-00008592 

Sample Number: 1300103-04 

Client Ref: Gemma 

Test 

Sulfur Speciation 

Ethyl Mercaptan 

Dimethyl Sulfide 

Carbon Disulfide 

2-Propanethiol 

tert-Butyl Mercaptan 

1-Propanethiol 

Thiophene 

Diethyl Sulfide 

n-Butyl Mercaptan 

Dimethyl Disulfide 

tetra-Hydro Thiophene 

n-Pentanethiol 

Diethyl Disulfide 

Total Unknown Mercaptan 

Total Reduced Sulfur 

Product: 

Location: 

Sample ID: 

Vessel: 

Method Result 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 <0.1 

AQMD 307/ASTM D5504 0.2 

AQMD 307/ASTM D5504 0.2 

Approved By: 

Natural Gas 

NG Line - 2 

Test #S2/NG Line-Fuel Sulfur-2 

Units 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

ppm vlv 

Signature On File 

Francine Hanby 

Laboratory Manager 

ISSlIer WBJT8111S that il has exercised du-e diligence and care with respect 10 !he informahon and professional judgmmts embodied in this reporl. TIlls report .,nCClS only the findings al the rime and place of inspection 

and tesllng. ISliuer expressly disclaims any further indemnity of any kind. This repon 15 1101 a llUaranlee or policy of insurance 'Hith respecl lO the goods or the ronlr.cwa! performance of any party. Any pc:r$OO relying 

upon this report should be aware thaI issuer's activities are carried out under thell general term.s and conditions. 

"Precision parameters IIjlPty in the evaluation or me lest results specified above. Please alS(l refer to ASTM 03244 (except for analysis ofRfG) iUld IP 367 with ICSp«t to the utilization of the leSI data to detennine 

confonTIlII1ce with specifications." 

Page 12 of 12 
APPENDIXC TEST DATA 

R041 0673 C-1 

Delta/'!.,. .. """ ..... :.... .. ..-.. 
Appendix C.1 Stratification and Preliminary Flow Rate Tests 

R0410673 C-2 
12-POINT STRATIFICATION CHECK 

Gemma 

2 

1/30/2013 

02 CO2 NOx CO 

Port Point % % ppm ppm 

W 3 13.52 4.24 1.59 0.09 

W 2 13.53 4.24 1.58 0.17 

W 13.56 4.23 1.64 0.20 

N 3 13.48 4.29 1.78 0.16 

N 2 13.48 4.29 1.81 0.23 

N 1 13.43 4.32 1.87 2.40 

E 3 1307 4.54 2.27 1.94 

E 2 13.08 4.53 2.35 1.91 

E 1 13.08 4.54 2.27 1.69 

S 3 13.08 4.54 2.34 1.12 

S 2 13.08 4.55 2.40 0.60 

S 1 13.07 4.55 2.53 0.57 

Average 13.3 4.4 2.0 0.9 

Maximum 13.6 4.6 2.5 2.4 

Minimum 13.1 4.2 1.6 0.1 

Maximum Difference from Average 0.3 0.2 0.5 1.5 

Max Difference (% of average) 2.0% 3.9% 24.2% 159.6% 

Criteria: 

If < 10%, use single point. 

Action Taken: 

12-point traverse used for RATA runs 

Runs in conjunction with NH3 test, use 12-point traverse 
RELATIVE ACCURACY TEST 

DATA AND WORKSHEET 

CPV Sentinel-2-CEMS-103·STRAT 

TEST CONSTANTS 

Station: CPV Sentinel 

Unit: 2 

Perfonned By: AA. SP. SS. JM 

Cp' 0.84 

Tref: 68 ' F 

Stack Area: 143.14 ft' 

MeterYd: 0.992 

METHOD 2.1 DATA 

dP Temp Vel. 

Point (in. H2O) sqrt(dP) OF (Ips) 

4 1.50 1.2247 758 105.25 

3 1.80 1.3416 759 115.34 

2 2.00 1.4142 760 121.63 

1 2.10 1.4491 760 124.63 

4 1.30 1.1 402 764 98.22 

3 1.40 1.1632 763 101.89 

2 1.50 1.2247 764 105.51 

1 1.80 1.3416 763 115.53 

4 1.50 1.2247 760 105.33 

3 1.80 1.3416 766 115.67 

2 2.20 1.4832 766 127.88 

1 3.00 1.7321 766 149.33 

4 1.60 1.2649 758 108.70 

3 1.70 1.3038 759 112.09 

2 1.80 1.34 16 766 11 5.67 

1 2.80 1.6733 766 144.27 

Average 1.8369 1.3553 762.4 116.68 

Stack Flow Rate: 1,002.1 kwacfm 

Stack Flow Rate: 397.9 kdscfm 

Dry Gas Meter 

Time Vol. Tm(in) Tm(out) #/Matl. 

Start 411 .600 74 70 H,O 

75 71 H,O 

76 71 Empty 

End 431 .290 I SG 

line Rinse 

Total 19.690 72.8 Total 

NOx ppm 

NOx , ppm@ 15% O2 

NOx IblMMBtu 

NOx Iblhr 

CO ppm 

CO, ppm@15%02 

CO Iblhr 

O2 % 

Stack Flow dscfh 

CT Fuel Flow hscfh 

Turbine Water Injection gpm 

8./18 RlrQUII1lY5.MCIIS 

1845 N. Case Street 

Orange, California 92865 

714-279-6777 

CT load MW 

SCR NH3 Injection Iblhr 

NOx IblMMSCF 

CO IbJMMBlu 

CO Ib/MMSCF 

TEST VARIABLES 

Start Date: 1/30/2013 

StarVEnd Time: 8,30 

Load (MW)lReplicate# 103 

Barom. Pressure: 29.80 

Pstack: 2.10 

Pstack: 29.95 

MW: 26.30 

METHOD 100.1 DATA 

0, Co, 

Analyzer Range 20 10 

Cal Gas Value 9.98 4.96 

Pre-Test Direct Zero 0.12 -0.02 

Pre-Test Direct Span 10.10 5.02 

Pre-Test System Zero 0.13 -0.01 

Pre-Test System Span 9.98 5.05 

Post-Test System Zero 0.18 0.07 

Post-Test System Span 10.01 5.13 

Post-Test Direct Zero 0.10 0.10 

Post-Test Direct Span 10.09 5.22 

Average 13.29 4.41 

Corr. results 13.32 4.29 

Pre-test zero bias 0.1% 0.2% 

Pre-test span bias -0.6% 0.3% 

Post-test zero bias 0.4% -0.3% 

Post-lest span bias -0.4% -0.9% 

Zero drift 0.2% 0.7% 

Span drift 0.1% 0.6% 

METHOD 4.1 DATA 

Impingers 

End Start Diff. 

811.1 679.2 131 .9 Meter Pressure: 

664.4 664.3 0.1 

563.4 583.4 0.0 Sample Volume: 

885.9 881.4 4.5 H20 Volume: 

100.0 -100.0 Moisture Content: 

36.5 

RESULTS 

Ref. Meth CEMS Diff. Ditt. % 

2.06 2.00 0.06 3.1'% 

161 1.50 0.11 6.6% 

0.006 0.006 0.000 0.0% 

5.89 4.96 0.93 15.7% 

0.77 0.90 -0.13 -16.9% 

0.60 0.66 -0.06 -10.2% 

1.34 1.29 0.05 3.4% 

13.32 13.20 0.12 0.9% 

23,676,927 21,076,000 2.800.927 11 .7% 

- 8,490.2 - - - - 103 -

- 110.0 - 6.93 

0.001 - 1.41 -

9,02 

STAAT 

iwg 

"H9 

Ib/lb-mole 

NO, CO 

5 10 

4.62 4.49 

0.00 0.Q1 

4.81 4.50 

0.00 0.25 

4.77 4.55 

~ 0.10 

4.75 4.51 

-0.01 0.04 

4.76 4.53 

2.04 0.92 

2.06 0.77 

-0.1% 2.5% 

-0.9% 0.5% 

0.2% 0.6% 

-0.4% -0.2% 

0.0% -1.5% 

-0.4% -0.4% 

1.6 iwg 

19.362 dscf 

1.723 scf 

8.2 % 

Sentinel Unit 2 RATA.xls 

21712013 

4:12 PM 
Port Point Angle 

W 4 2 

W 3 0 

W 2 4 

W 1 6 

N 4 3 

N 3 4 

N 2 5 

N 1 2 

E 4 4 

E 3 1 

E 2 3 

E 1 0 

S 4 2 

S 3 1 

S 2 4 

S 1 4 

Average 2.8 

Average Angle < 10 deg.? Yes 

No Points w/Reverse Flow? Yes 

Less Than 4 Points> 30 Oeg.? Yes 

PASS 
FLUE GAS VELOCITY DATA AND WORKSHEET 

CLIENT: Gq 61'" M ,::, PERFORMED BY: s? S P 

LOCATION: SeN \ \ f\J A L BAR. PRESSURE:--'Z"-'qi-.. '6"'D,,-.::=----------

UNIT: \J I\.J \ T :>- STATIC PRESSURE: __ "'-,2.~~~I ______ _ 

TEST DATE: I! 30 \ (7) TC READOUT 10:-->1;.... ' ·1.:....:::..V->_<.--'5~ ______ _ 

TEST NUMBER: S - "'-Sn<-- '-'II.- ioo:i TC 10: \ \ 

LEAK CHECK PRE- ./ POST-_/=--- PITOT'""T:::-U'-::BC=E:--:I~D-: ,&---r;Q7.9:-,-------

tlP INDICATOR TYPE: <'~ (o.o\\.lAt'~ PITOT TUBE COEFFICIENT:....:D=-:.!-'D"'-'t-l-·---, ___ _ 

tlP INDICATOR 10: P' < ZERO: v' LEVEL:----".-/==----___ _ 

Yaw Angle, tlP, Temperature, 

Time Port Point Degrees(1) inches H2O OF 

o£qo tV 1-) ... 2 -0 t ' 'S""" '7 <;7" , 

'7, < v' D \ -'b- I.'~; '1 

-z.. -l-\ ,O ~,O 'l C9C7 

>-C? -cJ 'J. ' \ 'l ron l~ Lj- ~] , 0 t ' -:;, I~'--f 

:> -r-L +.0 \ -'-i l 4>:) 

L., ... tf;'D ~, l.S- I l,-t..{ 

\ 'i- ;) .0 1. 0 '7403 

E::: t. .. '-\ " - 0 t ,S /l"U 

--; -1-),0 'L'b '/ r:ct/, 

L ... 3-0 ;;l, , d--. 'ltD0 

I I--b·0 3 . 0 7/_ (-, 

:5 y i.)<D 'Lw I <i<-6 

CJ.. "'l.O l , 1 "S'l 

2- ... <1--\ .D { d:? "'\ ("-<r 

I ..,.-L -u ,;,z.E? cG(P 

Comments: 1) Positive yaw angles correspond to clockwise rotation of the probe. 

J1eItaL\ ""---

Date of last revision 11/13/08 

D8834033 

Master Document 8torageiFormsiDatasheetsiFieid Datasheets 
WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET 

CLIENT: 6:! c {(\ {(\ ('r AMBIENT TEMPERATURE: '78 0 

LOCATION: c,,, ,,1< .. ,.,,,.... BAROMETRIC PRESSURE-: """':J.. """""g'-':7()--------

DATE: I) Je l'?> I ASSUMED MOISTURE: . 

RUN NO: <; -.l. -91"1< - NH,, '- Ic6- .p .. ,- tJ· PITOT TUBE COEFF. C'-p-: ;:-:--,7...,A .---------

OPERATOR: s. S~!V\ 1 - PROBE ID NO/MATERIAL: __ -tZ'--______ _ METER BOX NO: S p",,- P PROBE LENGTH: 7 

METER dH@: tj\';'L NOZZLE ID NO/ M:-:A-=T=ER=-I:-:-A-:-L:--: ,v:T/r ;"'--------

METER Yd: O.~"2: NOZZLE DIAMETER: 7 

STACK AREA, FT~ : FILTER NOffYPE: ---,7,L---------- TRAVERSE POINTS, MIN/POINT: ~ xl ~p PRE-TEST LEAK RATE:: < " ,et?LCFM@ / '5" in. Hg. 

dH= __ X dP: POST-TEST LEAK RATE: :.(o<'C7 CFM@ I 5" in. Hg. 

Probe Condition, pre/post test: PITOT LEAK CHECK - PRE: I'" /.+ POST: AI ~ 

Silica Gel Expended, YIN: CHAIN OF CUSTODY: SAMPLE CUSTODIAN • .-;::Y' 

Filter Condition after Test: Z SAMPLER '"3'5 ~ 

Check Weight: 7 SAMPLE CUSTODIAN-,.LLL 

Meter 

Point I Time I Volume, ft3 

-p I OCOX' I '-H\. i. 6(J 7 DV):J. /.-ffi) 

~~~ :3 1(') ~"?R I '-'di", , '-rz.v 

7 (~eJ 

I IOfl,"n. 

V ii? 

s To iA9:;;: 1\,-\ 2. r·i'fL 

t. 166Yt1 

i I Ot¢:5t 

V I 0 'f.:,<;,,) 

.-; 1 0 "081 1 L\ :2 c..>. 'i7tC 

~ l"'Wi 

b C,o\ 

I) 10QO?; I-\~"l. 'Z'1o 

Aver~e : 

dP 

in. H,O 

dH 

in. H,O 

(,y;.!, 

t· '6 

'l , '() 

Stack 

Temp. OF 

1'-'1'" 

/-

J( 

Probe 

Temp, OF 

t"A 

~ 

Filter 

Temp, OF 

IV Ir 

I 

1 

Imp. Out 

Temp, OF 

rf/l, 

S§ 

'3'5 

Imp. # Contents Post-Test - Pre-Test = Difference 

V,i tl \·hS:>-/ ,fIr \ rcl'1 ·Z. __ ':2- DIN lis'»' Ctv~·y( 1.4 ·3 c 

'3 w'\ 5vl'3.~S'63, 1 , 

l ~ ~ !r&>S,1 B0 1,Lj , 

vr \t-.s,o \"" 1,'12 \2.,'\.Se" - \DO 

Total: ____________ _ 

Meter Temp, OF 

In lOut 

1'-\ 1 ·-(U 

7'> 1 l \. 

,c" I "1( 

Vacuum 

in. Hg. 

"",.0 

"il 

0, 

% 

Pstatic 

in. H,O 

Comments: ____________________________________________________________________________________________________________ _ 

Date of last revision 11 /13/08 

D5834048 

Master Document 5torageiFormsiDatasheetsiFieid Datasheets 
Appendix C.2 CEM Data 

R0410673 C-3 De/tab. """"",,"",,,,, .. _ ... 
Appendix C.2.1 CEM Quality Assurance Measurements 

R0410673 C-4 Deltal'1 ,,""- ....... , .. -
Client: Gemma 

Delta AIr QualfIY Services 

CEMS PERFORMANCE DATA SHEET 

Location: CPV Sentinel Unit 2 

Date: 1/30/2013 

Performed By: AA, SP, SS, JM 

CEMS ID#: ..=5--=-C:.,:E::;.M;:.:S=--__________ _ 

Analyzer: O2 CO2 NO, CO 

Manufacturer: AMI CAl CAl TECO 

Serial Number: 021119-3 W06004-M V10043 CM0490048 

CEMS Probe: Material: S.S. Length: 8' 

Heated Line Material: Teflon Length: 6' 

Sample Conditioner: Type: Universal 

CEMS Line: Material: Teflon Length: 200' 

Bias Line: Material: Teflon Length: 200' 

Upscale Response Time: 30 Downscale Response Time: 

Sample Pressure (psi): 6 TECO Vacuum (oo Hg): 

Sample Flow Rate: 8 SCFH 

S02 

--

Gas Temp: 780 of 

Gas Temp: 275 of 

Gas Temp: 32 of 

30 seconds 

NA 

Sentinel Unit 2 CEMS QA.xls 

2/7/2013 

4:40 PM 
GAS 

Zero 

Zero 

NO 

NO 

N02 

N02 

Dllha AIr qua/flY S/ltv/C/IS 

N02 to NO Converter Efficiency Test 

Analyzer Manufacturer: 

Analyzer Model: 

Analyzer Serial Number: 

Date: 

ANALYZER 

MODE 

NO, 

NO 

NO, 

NO 

NO 

NO, 

Abs . Value Co-C,: 

Abs. Value C2-C,: 

C,/C2 

CE = 0,10, • 100%: 

Gemma CPV SentinEIIIOrUl<l! Gas Value: 4.82 

600CLD 

V10043 

1/30/13 

3.9 

3.7 

2% 

93% 

N02 Cal Gas Value: 4 .02 

ANALYZER 

RESPONSE 

0.00 

0.00 

4.82 

4.84 

0.08 

3.73 

Label 

0 , 

O2 

0 3 

Performed By: AA 

CEMS 10#: 5-CEMS 

CAL 

CORRECTED LABEL 

0.1 

3.7 

Requirement 

<5% 

>90% 

C, 

C2 

Sentinel Unit 2 CEMS QA.xls 

2/7/2013 

4:40 PM 
GAS 

Zero 

Zero 

NO 

NO 

NO, 

NO, 

OBlla Air Quality SBlfllcBS 

NO, to NO Converter Efficiency Test 

Analyzer Manufacturer: 

Analyzer Model: 

Analyzer Serial Number: 

Date: 

ANALYZER 

MODE 

NO, 

NO 

NO, 

NO 

NO 

NO, 

Abs. Value Co-C, : 

Abs. Value C,-C, : 

C,/C, 

CE = 0,/0, • 100%: 

Gemma CPV SentinEIIIOr1ila! Gas Value: 4.82 

600CLD 

V10043 

1/31/13 

4.0 

3.8 

0% 

96% 

NO, Cal Gas Value: 4.02 

ANALYZER 

RESPONSE 

-0.01 

-0.02 

4.82 

4.83 

0.00 

3.85 

Label 

0, 

0, 

0 3 

Performed By: AA 

CEMS 10#: 5-CEMS 

CAL 

CORRECTED LABEL 

0.0 

3.9 

Requirement 

<5% 

>90% 

C, 

C, 

Sentinel Unit 2 CEMS QA.xls 

2/7/2013 

4:40 PM 
GAS 

Zero 

Zero 

NO 

NO 

NO, 

NO, 

OeltJl AI, qualllY SeN/CBs 

NO, to NO Converter Efficiency Test 

Analyzer Manufacturer: 

Analyzer Model: 

Analyzer Serial Number: 

Date: 

ANALYZER 

MODE 

NO, 

NO 

NO, 

NO 

NO 

NO, 

Abs. Value Co-C, : 

Abs. Value C,-C,: 

C,/C, 

CE = 0,10, • 100%: 

Gemma CPV SentimlllOrUla! Gas Value: 4.82 

600CLD 

V10043 

2/1/13 

4.0 

3.8 

1% 

96% 

NO, Cal Gas Value: 4.02 

ANALYZER 

RESPONSE 

-0.03 

-0.03 

4.81 

4.82 

-0.01 

3.85 

Label 

0, 

0, 

0 3 

Performed By: AA 

CEMS 10#: 5-CEMS 

CAL 

CORRECTED LABEL 

0.0 

3.9 

Requirement 

<5% 

>90% 

C, 

C, 

Sentinel Unit 2 CEMS QA.xls 

2/7/2013 

4:40 PM 
Delta Air QualllY Services 

SPAN GAS RECORD AND SCAQMD CALIBRATION ERROR/LINEARITY 

CLiENT/LOCATION: Gemma CPV Sentinel Unit 2 

TRUCK/CEM 1.0.: .:::5....::-C::.:E"'M"'S'--__________ _ 

DATE: 1/30/13 

BY: AA, BF, SS,ME,JM 

Exp. Vendor %of 

Gas Cylinder # Value Date 10 Range 

ZERO Low CC93915 0.0 10/6/17 F22012 

0, Mid CC72997 9.98 11/16/15 F22012 49.9% 

0, High CC199067 18.90 4/4/15 F22012 94.5% 

CO, Mid CC72997 4.96 11 /16/15 F22012 49.6% 

CO, High CC199067 9.62 4/4/15 F22012 96.2% 

NO, Mid CC321491 2.58 1130/13 F22012 51 .6% 

NO, High CC362309 4.82 5/24/14 F22012 96.4% 

NO, NO, CC113404 4.02 7/9113 F22013 80.4% 

CO Mid CC325462 4.49 2/20/13 F22012 44.9% 

CO High CC313840 9.47 8/16/15 F22012 94.7% 

PRE-TEST INSTRUMENT CALIBRATION ERROR 

ANALYZER 

0, CO, NO, CO 

Analyzer Range 20 10 5 10 

Zero Gas Value 0.0 0.0 0.0 0.0 

Analyzer Reads 0.12 -0.02 0.00 0.01 

Error (% of scale) 0.6% -0.2% 0.1% 0.1% 

High Gas Value 18.90 9.62 4.82 9.47 

Analyzer Reads 18.97 9.64 4.81 9.51 

Error (% of scale) 0.3% 0.2% -0.2% 0.4% 

Mid Gas Value 9.98 4.96 2.58 4.49 

Analyzer Reads 10.10 5.02 2.56 4.50 

Error (% of scale) 0.6% 0.6% -0.3% 0.0% 

Linearity at Mid Point 0.2% 0.6% -0.3% -0.2% 

POST-TEST INSTRUMENT CALIBRATION ERROR 

ANALYZER 

0, CO, NO, CO 

Analyzer Range 20 10 5 10 

Zero Gas Value 0.0 0.0 0.0 0.0 

Analyzer Reads 0.10 0.12 -0.01 0.01 

Error (% of scale) 0.5% 1.2% -0.2% 0.1% 

High Gas Value 18.90 9.62 4.82 9.47 

Analyzer Reads 18.87 9.67 4.78 9.48 

Error (% of scale) -0.1% 0.5% -0.9% 0.1% 

Mid Gas Value 9.98 4.96 2.58 4.49 

Analyzer Reads 10.07 5.13 2.54 4.49 

Error (% of scale) 0.4% 1.7% -0.8% 0.0% 

Linearity at Mid Point 0.3% 0.9% -0.2% -0.1% 

STATUS 

--

--

PASS 

--

-- PASS 

--

--

PASS 

PASS 

STATUS 

--

-- PASS 

--

-- PASS 

--

-- PASS 

PASS 

Sentinel Unit 2 CEMS QA,xls 

2/7/2013 

4:39 PM 
00/18 Air QualllY SOMCOS 

SPAN GAS RECORD AND SCAQMD CALIBRATION ERROR/LINEARITY 

CLiENTILOCATION: Gemma CPV Senlinel Unit 2 

TRUCK/CEM I.D.: -,,5~-C~E::!:M:::S~ __________ _ 

DATE: 1131/13 

BY: AA,BF,SS,ME,JM 

Exp. Vendor %01 

Gas Cylinder # Value Date 10 Range 

ZERO Low CC93915 0.0 10/6/17 F22012 

0, Mid CC72997 9.98 11/16115 F22012 49.9% 

0, High CC199067 18.90 41411 5 F22012 94.5% 

CO, Mid CC72997 4.96 11/16115 F22012 49.6% 

CO, High CC199067 9.62 414115 F22012 96.2% 

NO, Mid CC321491 2.58 1130/13 F22012 51.6% 

NO, High CC362309 4.82 5124/14 F22012 96.4% 

NO, NO, CC113404 4.02 719113 F22013 80.4% 

CO Mid CC325462 4.49 2120/13 F22012 44.9% 

CO High CC313840 9.47 8116/15 F22012 94.7% 

PRE-TEST INSTRUMENT CALIBRATION ERROR 

ANALYZER 

0, CO, NO, CO STATUS 

Analyzer Range 20 10 5 10 

Zero Gas Value 0.0 0.0 0.0 0.0 -- Analyzer Reads 0.11 0.06 -0.01 0.00 - Error (% of scale) 0.5% 0.6% -0.3% 0.0% PASS 

High Gas Value 18.90 9.62 4.82 9.47 --

Analyzer Reads 18.98 9.66 4.79 9.44 -- Error (% of scale) 0.4% 0.4% -0.6% -0.3% PASS 

Mid Gas Value 9.98 4.96 2.58 4.49 --

Analyzer Reads 10.10 5.09 2.54 4.46 -- Error (% of scale) 0.6% 1.3% -0.8% -0.3% PASS 

Linearity at Mid Point 0.2% 0.8% -0.3% -0.2% PASS 

POST-TEST INSTRUMENT CALIBRATION ERROR 

ANALYZER 

0, CO, NO, CO STATUS 

Analyzer Range 20 10 5 10 

Zero Gas Value 0.0 0.0 0.0 0.0 -- Analyzer Reads 0.09 0.09 0.04 -0.07 -- Error (% of scale) 0.5% 0.9% 0.8% -0.7% PASS 

High Gas Value 18.90 9.62 4.82 9.47 -- Analyzer Reads 18.79 9.67 4.76 9.35 -- Error (% of scale) -0.5% 0.5% -1.3% -1 .2% PASS 

Mid Gas Value 9.98 4.96 2.58 4.49 --

Analyzer Reads 10.04 5.13 2.54 4.39 -- Error (% of scale) 0.3% 1.7% -0.8% -1 .0% PASS 

linearity at Mid Point 0.3% 1.0% -0.5% -0.1% PASS 

Note. NOx analyzer linearity IS greater than the SCAQMD Method 100.1 speclficallon of +I-d % b~~ c 

within the uncertainty (+1-2%) of the best available calibration standards available fa the rangg'irri' usn~'.2 EM;/~O~ ; 

4:39 PM 
Delta A1rqualfIY So/VIces 

SPAN GAS RECORD AND SCAgMD CALIBRATION ERROR/LINEARITY 

CLiENT/LOCATION: Gemma CPV Sentinel Unit 2 

TRUCK/CEM 1.0.: ..::5c.:-C"'E:::M"'S=-__________ _ 

DATE: ..::.2/,::1 :..: 11:::3 :-::-::-:-=--::-:-_ 

BY: AA, BF, SS, ME, JM 

Exp, Vendor %of 

Gas Cylinder # Value Date 10 Range 

ZERO Low CC93915 0.0 10/6/17 F22012 

O2 Mid CC72997 9.98 11 /16/15 F22012 49.9% 

O2 High CC199067 18.90 4/4/1 5 F22012 94.5% 

CO2 Mid CC72997 4.96 11 /16/15 F22012 49.6% 

CO2 High CC199067 9.62 4/4/15 F22012 96.2% 

NO, Mid CC321491 2.58 1/30/13 F22012 51 .6% 

NO, High CC362309 4.82 5/24/14 F22012 96.4% 

N02 N02 CC113404 4.02 7/9113 F22013 80.4% 

CO Mid CC325462 4.49 2/20/13 F22012 44.9% 

CO High CC313840 9.47 8/16/15 F22012 94.7% 

PRE-TEST INSTRUMENT CALIBRATION ERROR 

ANALYZER 

O2 CO2 NO, CO 

Analyzer Range 20 10 5 10 

Zero Gas Value 0.0 0.0 0.0 0.0 

Analyzer Reads 0.10 -0.02 -0.02 -0.03 

Error (% of scale) 0.5% -0.2% -0.4% -0.3% 

High Gas Value 18.90 9.62 4.82 9.47 

Analyzer Reads 19.14 9.66 4.79 9.45 

Error (% of scale) 1.2% 0.4% -0.7% -0.2% 

Mid Gas Value 9.98 4.96 2.58 4.49 

Analyzer Reads 10.19 5.05 2.54 4.52 

Error (% of scale) 1.1% 0.9% -0.8% 0.3% 

Linearity at Mid Point 0.2% 0.8% -0.3% 0.5% 

POST-TEST INSTRUMENT CALIBRATION ERROR 

ANALYZER 

O2 CO2 NO, CO 

Analyzer Range 20 10 5 10 

Zero Gas Value 0.0 0.0 0.0 0.0 

Analyzer Reads 0.10 0.03 -0.02 -0.04 

Error (% of scale) 0.5% 0.3% -0.4% -0.4% 

High Gas Value 18.90 9.62 4.82 9.47 

Analyzer Reads 19.02 9.70 4.77 9.43 

Error (% of scale) 0.6% 0.8% -1.1% -0.4% 

Mid Gas Value 9.98 4.96 2.58 4.49 

Analyzer Reads 10.13 5.11 2.52 4.43 

Error (% of scale) 0.8% 1.5% -1.1% -0.6% 

Linearity at Mid Point 0.2% 0.9% -0.4% -0.2% 

STATUS 

--

-- PASS 

--

--

PASS 

--

-- PASS 

PASS 

STATUS 

--

-- PASS 

--

--

PASS 

--

-- PASS 

PASS 

Sentinel Unit 2 CEMS QA.xls 

21712013 

4:39 PM 
Source 

Test Date 

AETB Name 

AETB Phone Number 

AETB e-mail 

QI Last Name 

QI First Name 

QI Middle Initial 

QI Exam Date 

Exam Provider 

Exam Contact 

Gemma CPV Sentinel Unit 2 

1/30/2013 

Delta Air Quality Services, Inc. 

714-279-6777 

contact@deltaags.com 

Aleshaiker 

Ali 

M 

November 21 , 2008 

Source Evaluation Society 

gstiprogram@gmail.com 
Appendix C.2.2 NOx and CO Compliance 

R0410673 C-5 
COMPLIANCE TEST 

DATA AND WORKSHEET 

CPV Sentlnel-2-CEMS-50-1 

TEST CONSTANTS 

Station: CPV Sentinel 

Unit 2 

Performed By: AA, SP, SS, JM 

Cp: 0.99 

Tref: 60 of 

Stack Area: 143.14 ft' 

Meter Yd: 0.992 

METHOD 2.1 DATA 

dP Temp Vel. 

Point (in. H2O) sqrt(dP) of (fps) 

4 0.61 0.7810 774 79.99 

3 0.65 0.8062 773 82.54 

2 0.72 0.8485 772 86.B3 

1 0.75 0.8660 772 88.63 

4 0.60 0.7746 770 79.20 

3 0.59 0.7681 773 78.64 

2 0.63 0.7937 776 8'-36 

1 0.65 0.8062 775 82.61 

4 0.60 0.7746 771 79.24 

3 0.63 0.7937 770 81 .16 

2 0.72 0.8485 776 86.98 

1 0.83 0.9110 777 93.42 

4 0.71 0.8426 774 86.30 

3 0.88 0.9381 777 96.19 

2 0.95 0.9747 778 99.99 

1 0.85 0.9220 779 94.62 

Average 0.7066 0.8406 774.2 86.11 

Stack Flow Rate: 739.5 kwacfm 

Stack Flow Rate: 282.3 kdscfm 

Dry Gas Meter 

Time Vol. Tm(in) Tm(out) #/Matl. 

Start 924.138 80.5 77.9 H,O 

84.0 79.0 H,O 

End 972.196 83.0 79.0 Empty 

82.0 80.0 SG 

Total 48.058 80.7 Total 

NO .. ppm 

NO~, ppm @ 15% O2 

NO .. IblMMBtu 

NO .. Iblhr 

CO ppm 

CO, ppm @ 15% O2 

CO Ib/hr 

0, % 

Stack Flow dscfh 

CT Fuel Flow hscfh 

Turbine Water Injection gpm 

8,118 All Qua/flY StlIIIICls 

1845 N. Case Street 

Orange, California 92865 

7 14-279-6777 

CT Load MW 

SCR NH3 Injection lblhr 

NO .. IblMMSCF 

CO Ib/MMBtu 

CO Ib/MMSCF 

TEST VARIABLES 

Start Date: 2/1/13 

Start/End Time: 14:20 15:35 

Load (MW)/Replicate# 50 1 

Barom. Pressure: 29.69 

Pslack: 

Pstack: 

MW: 

Analyzer Range 

Cal Gas Value 

Pre-Test Direct Zero 

Pre-Test Direct Span 

Pre-Test System Zero 

Pre-Test System Span 

Post-Test System Zero 

Post-Test System Span 

Post-Test Direct Zero 

Post-Test Direct Soan 

Average 

Corr. results 

Pre-test zero bias 

Pre-test span bias 

Post-test zero bias 

Post-test span bias 

Zero drift 

Soan drift 

METHOD 4.1 DATA 

Impingers 

End Start Diff. 

861.4 682.7 178.7 

666.8 663.2 3.6 

583.3 582.5 0.8 

916.8 900.6 16.2 

Ir 100 99.3 

RESULTS 

Ref. Meth CEMS 

2.20 2.10 

1.99 1.85 

0.007 0.01 

4 .52 3.84 

0.26 0.30 

0.23 0.26 

0.32 0.48 

14.38 14.33 

16,936,600 15,604.000 

- 5,361 

55 

- 107 

8.44 -

0,001 - 0.55 -

2.10 mg 

29.84 "H9 

28.1 4 lb/lb-mole 

METHOD 100.1 DATA 

0, CO, NO, CO 

20 10 5 10 

9.98 4.96 4.82 4.49 

0.07 0.25 -0.03 -0.03 

10.04 5.40 4.73 4.44 

0.17 0.31 -0.02 0.14 

10.04 5.39 4.71 4.39 

0.21 0.31 -0.03 0.08 

10.03 5.36 4.69 4.39 

0.09 0.25 -0.04 -0.04 

10.09 5.40 4.74 4.43 

14.38 4.09 2.14 0.35 

14.38 3.70 2.20 0.26 

0.5% 0 .6% 0.3% 1.7% 

0.0% -0.2% -0.4% -0.5% 

0.6% 0.6% 0.1% 1.2% 

-0.3% -0.4% -1.0% -0.4% 

0.2% 0.0% -0.2% -0.6% 

-0.1% -0.2% -0.4% 0.0% 

Meter Pressure: 1.8 iwg 

Sample Volume: 45.700 dscf 

H20 Volume : 4.616 scf 

Moisture Content: 9.2 % 

Sentinel Unit 2 50% NOx·NH3-ROG Compliance. xis 

2/7/2013 

4:18PM 
COMPLIANCE TEST 

DATA AND WORKSHEET 

CPV SenUnel-2-CEMS-SO-2 

TEST CONSTANTS 

Station: CPV Sentinel 

Unit: 2 

Performed By: M , SP, SS, JM 

Cp: 0.99 

Tref: 60 "F 

Stack Area: 143.14 tt' 

Meter Yd: 0.992 

METHOD 2.1 DATA 

dP Temp Vel. 

Point (in.H.p) sqrt(dP) "F (Ips) 

4 0.63 0.7937 780 61 .55 

3 0.85 0.9220 782 94.60 

2 0.95 0.9747 781 100.16 

1 0.90 0.9467 780 97.47 

4 0.59 0 ,7661 779 76.66 

3 0.64 0 .6000 780 82.19 

2 0.80 0.8944 780 91 .89 

1 0.80 0.8944 78 1 91 .93 

4 0.59 0.7681 777 78.82 

3 0.55 0.74 16 778 76. 13 

2 0.63 0 .7937 774 81 .35 

1 0.60 0.7746 779 79.55 

4 059 0 .7661 780 78.92 

3 0.60 0.7746 781 79.61 

2 0.69 0.8307 78 1 85.38 

1 0.79 0.8888 781 91 .35 

Average 0.6947 0.8335 779.6 85.63 

Stack Flow Rate: 735.4 kwacfm 

Stack Flow Rate: 278.4 kdscfm 

Dry Gas Meter 

Time Vol. Tm(in) Tm(out) #/Matl. 

Start 975.178 80 78 H,O 

80 76 H,O 

End 10 19.529 80 78 Empty 

80 75 SG 

Total 44.351 78.4 Total 

NO~ ppm 

NO~, ppm @ 15% O2 

NO~ fb/MMBtu 

NO~ Iblhr 

CO ppm 

CO, ppm@ 15% O2 

CO Iblhr 

O2 % 

Stack Flow dscfh 

CT Fuel Flow hscfh 

Turbine Water Injection gpm 

Dllta AIr quality SIMCIS 

184 5 N. Case Street 

Orange, California 9286 5 

71 4-279-6777 

CTLoad MW 

SCR NH3 Injection Iblhr 

NO. IblMMSCF 

CO IblMMBtu 

CO IblMMSCF 

TEST VARIABLES 

Start Date: 211113 

Start/End Time: 15:53 17:09 

Load (MW)lReplicale# 50 2 

Barom. Pressure: 29.69 

Pstack: 

Pstack: 

MW: 

Analyzer Range 

Cal Gas Value 

Pre-Test Direct Zero 

Pre-Test Direct Span 

Pre-Test System Zero 

Pre-Test Svstem Span 

Post·Test System Zero 

Post-Test Svstem Span 

Post· Test Direct Zero 

Post-Test Direct !?pan 

Average 

Carr. results 

Pre-test zero bias 

Pre-test span bias 

Post-lest zero bias 

Post-test span bias 

Zero drift 

§pan drift 

METHOD 4.1 DATA 

Impingers 

End Start Oiff. 

787.3 606.6 160.7 

706.8 703.5 3.3 

657.8 656A lA 

968.9 958.3 10.6 

Ir 100 96.0 

RESULTS 

Ref. Meth CEMS 

2.27 2.10 

2.05 1.90 

0008 0.0 1 

4.59 3.99 

0.30 0.30 

0.27 0.25 

0.37 0.44 

14.36 14.32 

16,701 ,357 15,653,000 

5,391 

-

- 56 

- 107 

8.52 

0.001 

0.64 

2,10 "9 

29.84 'H9 

26. 10 Ib/lb-mole 

METHOD 100.1 DATA 

0, CO, NO, CO 

20 10 5 10 

9.98 4.96 4.82 4.49 

0.09 0.25 -0.04 -0.04 

10.09 5.40 4.74 4.43 

0.21 0.31 -0.03 0.08 

10.03 5.36 4.69 4.39 

0.21 0.19 -0.01 0 .13 

10.11 5.24 4.72 4.38 

0.10 0 .14 -0.02 -0.04 

10.11 5.25 4.77 4.43 

14.40 4.03 2.20 0.39 

14.36 3.71 2.27 0.30 

0.6% 0.6% 0.1% 1.2% 

-0.3% -0.4% -1 .0% -0.4% 

0.5% 0.6% 0.2% 1.7% 

0.0% 0.0% -1.0% -0.5% 

0.0% -1 .1% 0.5% 0.5% 

0.4% - 1.2% 0.5% 0.0% 

Meter Pressure: 1.6 iwg 

Sample Volume: 42.332 dscf 

H20 Volume : 4.463 scf 

Moisture Content 9.5 % 

Sentinel Unit 2 50% NOx-NH3·ROG Compliance.xls 

21712013 

4:18PM 
COMPLIANCE TEST 

DATA AND WORKSHEET 

CPV Sentinel-2-CEMS-75-1 

TEST CONSTANTS 

Station: CPV Sentinel 

Unit: 2 

Performed By: M,SP,SS, JM 

Cp' 0.99 

Tref: 60 "F 

Stack Area: 143.14 f1' 

MeterY,,: 0.992 

METHOD 2.1 DATA 

dP Temp Vel. 

Point (in. H2O) sqrt(dP) "F (Ips) 

4 0.65 0.6062 790 63.05 

3 0.61 0.9000 769 92.66 

2 0.95 0.9747 790 100.41 

1 1.20 1.0954 790 11 2.85 

4 0.66 0.8246 766 64.68 

3 0.68 0.6246 767 84.85 

2 0.71 0.6426 769 86.77 

1 0.72 0.6465 769 67.38 

4 0.65 0.6062 766 82.99 

3 0.72 0.8485 769 67.38 

2 0.63 0.91 10 790 93.65 

1 095 0.9747 790 100.41 

4 0.78 0.8832 790 90.98 

3 1.20 1.0954 791 112.69 

2 1.20 1.0954 792 112.94 

1 1.00 1.0000 792 103.10 

Average 0.6477 0.9207 789.6 94.64 

Stack Flow Rate: 814.5 kwacfm 

Stack Flow Rate: 306.8 kdscfm 

Dry Gas Meter 

Time Vol. Tm(in) Tm(oul) #/Mall. 

Start 822.650 70.6 72.3 H,O 

76.3 74.2 H,O 

End 666.694 63.5 77.7 Empty 

69.2 84.7 SG 

Total 44.244 76.6 Total 

NOx ppm 

NO., ppm@ 15% O2 

NO. IblMMBtu 

NOK tblhr 

CO ppm 

CO, ppm@ 15% O2 

CO Iblhr 

O2 % 

Stack Flow dscfh 

CT Fuel Flow hscfh 

Turbine Water Injection gpm 

DB/18 All qua/flY SBtrlCilS 

1845 N. Case Street 

Orange, California 92865 

714-279-6777 

CTLoad MW 

SCR NH3 Injection Iblhr 

NOx IbfMMSCF 

CO IblMMBtu 

CO IblMMSCF 

TEST VARIABLES 

Start Date: 2/1/13 

Start/End Time: 9,10 10:34 

Load (MW)/Repticate# 75 1 

Barom. Pressure: 29.69 

Pstack: 

Pstack: 

MW: 

Analyzer Range 

Cal Gas Value 

Pre-Test Direct Zero 

Pre-Test Direct Span 

Pre-Test System Zero 

Pre-Test System Span 

Post-Test System Zero 

Post-Test System Span 

Post-Test Direct Zero 

Post-Test Direct Span 

Average 

Corr. results 

Pre-test zero bias 

Pre-test span bias 

Posl-test zero bias 

Post-test span bias 

Zero drift 

Span drift 

METHOD 4.1 DATA 

Impingers 

End Start Diff. 

859.1 660.5 178.6 

674.6 671.4 3.2 

579.9 579.0 0.9 

932.5 922.6 9.9 

Ir 100 92.6 

RESULTS 

Ref. Meth CEMS 

2.66 2.50 

2.27 1.96 

0.006 0.007 

6.36 5.24 

0.47 0.70 

0.36 0.51 

0.63 0.73 

13.47 13.41 

18.407,808 17,635,000 

- 6,912 

-

- 60 

- 110 

9.23 - 0.001 - 0.66 -

2.10 iwg 

29.64 "Hg 

26.16 Jb/lb-mole 

METHOD 100.1 DATA 

0, CO, NO, CO 

20 10 5 10 

9.96 4.96 4.82 4.49 

0. 10 -0.02 -0.02 -0.03 

10.19 5.05 4.79 4.52 

0.17 0.11 -0.03 0.16 

10.04 5.06 4.74 4.45 

0.22 0.18 -0.02 0.16 

10.10 5.25 4.71 4.43 

0.10 0.13 -0.03 -0.02 

10.07 5.26 4.76 4.45 

13.53 4.43 2.80 0.62 

13.47 4.24 2.66 0.47 

0.3% 1.3% -0.2% 1.9% 

-0.8% 0.3% -1 .0% -0.7% 

0.6% 0.5% 0.3% 2.0% 

0.2% -0.1% -0.9% -0.2% 

0.3% 0.7% 0.2% 0.2% 

0.3% 1.7% -0.5% -0. 2% 

Meter Pressure: 1.9 iwg 

Sample Volume: 42.226 dscf 

H20 Volume : 4.304 scf 

Moisture Content: 9.3 % 

Sentinel Unit 2 75% NOx-NH3-ROG Compliance.xls 

2(7/2013 

4:18 PM 
COMPLIANCE TEST 

DATA AND WORKSHEET 

CPV Sentlnel·2-CEMS·75-2 

TEST CONSTANTS 

Station: CPV Sentinel 

Unil: 2 

Performed By: AA. SP. SS. JM 

Cp' 0.99 

Tref: 60 'F 

Stack Area: 143.14 ft' 

MelerYd: 0.992 

METHOD 2.1 DATA 

dP Temp Vel. 

Point (in. H2O) sQrt(dP) 'F (fps) 

4 0.73 0.8544 797 88,41 

3 1.20 1.0954 798 11 3.40 

2 1.20 1.0954 798 113.40 

1 1.10 1.0488 799 108.62 

4 0.65 0.8062 796 83.40 

3 0.70 0.8367 796 86.54 

2 1.10 1.0488 795 108.45 

1 1.20 1.0954 794 113.22 

4 0.63 0.7937 795 82.07 

3 0.65 0.8062 794 83.33 

2 0.63 0.7937 794 82.04 

1 0.65 0.8062 793 83.30 

4 0.68 0.8246 794 85.23 

3 0.72 0.8485 795 87.74 

2 0.83 0.911 0 795 94.20 

1 0.90 0.9487 795 98.09 

Average 0.8343 0.9134 795.5 94.46 

Stack Flow Rate: 811 .3 kwacfm 

Stack Flow Rate: 301.4 kdscfm 

Dry Gas Meter 

Time Vol. Tm(in) Tm(out) #/Matl. 

Start 868.920 86.0 80.9 H,O 

86.5 80.5 H,O 

End 917.834 85.0 77.5 Empty 

85.0 80.5 SG 

Total 48.914 82.7 Tolal 

NO~ ppm 

NO~, ppm@ 15% O2 

NO~ IblMMBtu 

NO~ Iblhr 

CO ppm 

CO, ppm@ 15% O2 

CO Iblhr 

O2 % 

Slack Flow dscfh 

CT Fuel Flow hscfh 

Turbine Water Injection gpm 

8,ItaAhQu.,/tYS,rr1C8I 

1845 N. Case Street 

Orange, California 92865 

714-279-6777 

CT Load MW 

SCR NH3 In'ection Iblhr 

NO~ IblMMSCF 

CO IbfMMBtu 

CO IblMMSCF 

TEST VARIABLES 

Start Dale: 211113 

Start/End Time: 11 :05 12:15 

Load (MW)/Replicate# 75 2 

Barom. Pressure: 29.69 

Pstack: 

Pstack: 

MW: 

Analyzer Range 

Cal Gas Value 

Pre-Test Direct Zero 

Pre-Test Direct Span 

Pre-Test System Zero 

Pre-Test System Span 

Post-Test System Zero 

Post-Test System Span 

Post-Test Direct Zero 

Post·Test Direct Span 

Average 

Carr. results 

Pre-test zero bias 

Pre-test span bias 

Post-test zero bias 

Post-test span bias 

Zero drift 

Span drift 

METHOD 4.1 DATA 

Impingers 

End Start Diff. 

882.4 684.3 198.1 

669.4 666.4 3.0 

488.5 487.5 1.0 

960.9 951.2 9.7 

I, 100 111 ,8 

RESULTS 

Ref. Meth CEMS 

2.78 2.50 

2.16 1.95 

0.008 0.007 

6.09 5.09 

0.86 0.90 

0.67 0 .72 

1,13 1.12 

13.32 13.40 

18,083,506 17,671,000 

- 6.936 

- I 

80 • - 110 

8.78 - 0.002 -

1.58 -

2.10 iwg 

29.84 "Hg 

28.06 Ib/lb-mole 

METHOD 100.1 DATA 

0 , CO, NO, CO 

20 10 5 10 

9.98 4.96 4.82 4,49 

0.10 0.13 -0.03 -0.02 

10.07 5.26 4.76 4.45 

0.22 0.18 -0.02 0.18 

10.10 5.25 4.71 4.43 

0.20 0.25 -0.01 0.15 

10.12 5.32 4.71 4.43 

0.09 0.20 -0.04 -0.02 

10.06 5.34 475 4.43 

13.41 4.55 2.71 0.98 

13.32 4.25 2.78 0.86 

0.6% 0.5% 0.3% 2.0% 

0.2% .Q.1% ·0.9% -0.2% 

0.5% 0.5% 0.6% 1.7% 

0.3% -0.2% ·0.8% -0.1% 

-0.1% 0.7% 0.3% -0.3% 

0.1% 0.7% .Q.1% 0 .0% 

Meter Pressure: 2,1 iwg 

Sample Volume: 46.369 dscf 

H20 Volume : 5.197 scf 

Moisture Conlent: 10.1 % 

Sentinel Unit 2 75% NOx-NH3·ROG Compliance. xis 

217/2013 

4:18 PM 
COMPLIANCE TEST 

DATA AND WORKSHEET 

CPV Sentinel-2-CEMS-100-1 

TEST CONSTANTS 

Station: CPVSentinel 

Unit: 2 

Performed By: AA. 5P. 55. JM 

Cpo 0.99 

Tref: 60 of 

Stack Area· 143.14 ft' 

Meter Y,,: 0.992 

METHOD 2.1 DATA 

dP Temp Vel. 

Point (in. H2O) sqrt(dP) of (fps) 

4 1.20 1.0954 773 112.12 

3 1.60 1.2649 774 129.52 

2 1.60 1.2649 775 129.58 

1 1.30 1.1402 774 116.75 

4 0.80 0.8944 775 91.62 

3 0.91 0.9539 772 97.60 

2 1.30 1.1402 772 116.66 

1 1.20 1.0954 773 112.12 

4 0.70 0.8367 770 85.53 

3 0.85 0.9220 770 94.25 

2 0.95 0.9747 770 99.64 

, 1.00 1.0000 771 102.27 

4 0.72 0 .8485 772 86.82 

3 0.74 0.8602 771 87.98 

2 1.00 1.0000 772 102.31 

, 1. 10 1.0488 772 107.31 

Average 1.0430 1.0213 772.3 104.51 

Stack Flow Rate: 897.5 kwacfm 

Stack Flow Rate: 339.7 kdscfm 

Dry Gas Meter 

Time Vol. Tm(in) Tm(out) #/Matl. 

Start 435.850 81 77 H,O 

77.5 72.5 H,O 

End 485.200 79 73 Empty 

75 72 5G 

Total 49.350 75.9 Total 

NO~ ppm 

NOx , ppm @ 15% O2 

NO~ Ib/MM8tu 

NO~ Iblhr 

CO ppm 

CO, ppm @ 15% O2 

CO Ibfhr 

O2 % 

Stack Flow dscfh 

CT Fuel Flow hscfh 

Turbine Water Injection gpm 

881ta AIr Qua/flY S8nt1CIIS 

1845 N. Case Street 

Orange, California 92865 

714·279·6777 

CT Load MW 

SCR NH3 Injection Iblhr 

NO~ IbfMMSCF 

CO IblMMBtu 

COlblMM5CF 

TEST VARIABLES 

Start Oate: 1/30/13 

Start/End Time: 11 :01 12:17 

Load (MW)lReplicate# 100 1 

Barom. Pressure: 29.80 

Pstack: 

Pstack: 

MW: 

Analyzer Range 

Cal Gas Value 

Pre-Test Direct Zero 

Pre-Test Direct Span 

Pre-Test System Zero 

Pre-Test System Span 

Post-Test System Zero 

Post-Test Svstem Span 

Post-Test Direct Zero 

Post-Test Direct Span 

Average 

Carr. results 

Pre-test zero bias 

Pre-test span bias 

Post-test zero bias 

PosHest span bias 

Zero drift 

Span drift 

METHOD 4.1 DATA 

Impingers 

End Start Diff. 

887.1 689.3 197.8 

669.0 6632 5.8 

490.3 489.9 0.4 

944.8 930.4 14.4 

I, 100 118.4 

RESULTS 

Ref. Meth CEM5 

3.34 

2.49 

0.009 

8.25 

2.96 

2.21 

4.39 

12.98 

20,384,677 

· 8.43B 

· r · 103 

· 110 

9.78 · 0.005 · 5.19 · 

2.00 iwg 

29.95 "H9 

2B.06 Ib/lb-mole 

METHOD 100.1 DATA 

0, CO, NO, CO 

20 10 5 10 

9.98 4.96 4.82 4.49 

0.10 0.10 ·0.01 0.04 

10.09 5.22 4.76 4.53 

0.12 0.12 -0.01 0.25 

10.09 5.22 4.74 4.53 

0.12 0.15 -0.01 0.19 

9.99 5.25 4.71 4.49 

0.10 0.12 -0.01 0.06 

9.94 5.25 4.79 4.54 

13.02 4.66 3.27 3.05 

12.98 4.40 3.34 2.96 

0.1% 0.2% 0.0% 2.1% 

0.0% 0.0% -0.5% 0.0% 

0.1% 0.3% 0.0% 1.3% 

0.2% 0.0% -1 .5% -0.5% 

0.0% 0.3% -0.1% -0.6% 

-0.5% 0.3% -0.6% -0.3% 

Meter Pressure: 1.8 iwg 

Sample Volume: 47.521 dscf 

HzOVolume : 5.504 scf 

Moisture Content: 10.4 % 

Sentinel Unit 2 100% NOx-NH3-ROG Compliance.xls 

217/2013 

4:18 PM 
COMPLIANCE TEST 

DATA AND WORKSHEET 

CPV Sentlnel-2-CEMS-100-2 

Station: 

Unit: 

CPV Sentinel 

2 

Performed By: AA, SP, SS, JM 

Cp: 0.99 

Tref: 

Stack Area: 

Meter 

3 0.90 

2 0.99 

1.30 

4 0.70 

3 0.82 

2 0.90 

0.85 

4 085 

3 1.00 

2 1.30 

1 1.50 

4 1.10 

3 1.50 

2 1.60 

Average 

Flow Rate: 

I 

Time 

Start 486.580 

End 534.400 

0.9487 

0.9950 

1.1402 

0.6367 

0.9055 

0.9487 

0.9220 

0.9220 

1.0000 

1.1402 

1.2247 

1.0488 

1.2247 

1.2649 

60 

143,14 

0.992 

774 

775 

776 

775 

775 

776 

778 

775 

776 

778 

779 

777 

778 

780 

OF 

ft' 

97.12 

101.90 

116.82 

85.69 

92.74 

97.20 

94.54 

94.42 

102.45 

116.91 

125.63 

107.50 

125.58 

129.81 

91 1.7 kwaefm 

#/Matl. 

69 69 H2O 

69 67 H2O 

67 68 Empty 

NOx ppm 3.03 

NOx , ppm@ 15% O2 2.25 

NOx IbIMMBtu 0.008 

NOx Iblhr 7.58 

CO ppm 2.12 

CO, ppm@ 15% O2 1.58 

CO Ib/hr 3.18 

O2 % 12.97 

I 

Turbine Water Injection gpm 

CTLoad MW 

SCR NH3 I Ib/hr 

NOx Ib/MMSCF 8.98 

CO IblMMBtu 0.004 

8.118111' QualItY S8111fC6S 

1845 N. Case Street 

Orange. California 92865 

714·279·6777 

Date: 

Sta rt/End Time: 13:11 15:05 

Load (MW)/Replicate# 100 2 

Barom. Pressure: 29.80 

Pstaek: 2.00 iwg 

Pstaek: 29.95 ·Hg 

MW: 

Pre-test zero bias 0.1% 0.3% 0.0% 1.3% 

Pre-lest span bias 0.2% 0.0% -1 .5% -0.5% 

Post-test zero bias 0.1% 0.2% 0.2% 2.0% 

Post-test span bias 0,0% 0.0% -0.2% 0.1 % 

drift 0.0% 0.9% 0,2% 0.1% 

Pressure: 2.0 iwg 

46.802 dscf 

5.392 sef 

Content: 10.3 % 

Sentinel Unit 2100% NOx-NH3-ROG Complianee.xls 

217/2013 

4:18PM 
Port 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

Average 

Point 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

Date 

2/1/2013 

2/1/2013 

21112013 

211/2013 

211/2013 

211/2013 

211 /2013 

211/2013 

211/2013 

2/1/2013 

2/1/2013 

21112013 

21112013 

2/1/2013 

21112013 

211 /2013 

211/2013 

211/2013 

2/1/2013 

21112013 

211 /2013 

21112013 

211/2013 

21112013 

211/2013 

211/2013 

211/2013 

2/1/2013 

2/1/2013 

21112013 

211/2013 

211/2013 

211/2013 

211/2013 

211/2013 

211/2013 

211/2013 

2/1/2013 

2/1/2013 

21112013 

211/2013 

21112013 

21112013 

21112013 

211/2013 

211/2013 

211/2013 

211/2013 

21112013 

211/2013 

21112013 

211/2013 

21112013 

211/201 3 

2/1/2013 

2/1/2013 

2/1/2013 

21112013 

211/2013 

21112013 

IlIhaA/rOua/1IY SIIMellS 

1845 N. Case Street 

Orange, California 92865 

714·279·6777 

Time 

14:21 

14:22 

14:23 

14:24 

14:25 

14:26 

14:27 

14:28 

14:29 

14:30 

14:31 

14:32 

14:33 

14:34 

14:35 

14:40 

14:41 

14:42 

14:43 

14:44 

14:45 

14:46 

14:47 

14:48 

14:49 

14:50 

14:51 

14:52 

14:53 

14:54 

15:02 

15:03 

15:04 

15:05 

15:06 

15:07 

15:08 

15:09 

15:10 

15:11 

15:12 

15:13 

15:14 

15:15 

15:16 

15:21 

15:22 

15:23 

15:24 

15:25 

15:26 

15:27 

15:28 

15:29 

15:30 

15:31 

15:32 

15:33 

15:34 

15:35 

REFERENCE METHOD 1·MINUTE AVERAGE DATA 

14.364 4.112 1.941 0.271 

14.373 

14.397 

14.394 

14.383 

14.368 

14.368 

14.363 

14.363 

14.372 

14.366 

14.38 

14.371 

14.382 

14.359 

14.38 

14.382 

14.385 

14.392 

14.385 

14.387 

14.391 

14.375 

14.377 

14.368 

14.341 

14.306 

14.308 

14.299 

14.304 

14.35 

14.345 

14.342 

14.349 

14.345 

14.344 

14.345 

14.348 

14.342 

14.342 

14.348 

14.349 

14.344 

14.346 

14.345 

14.398 

14.391 

14.39 

14.392 

14.398 

14.421 

14.434 

14.427 

14.44 

14.427 

14.437 

14.44 

14.462 

14.452 

14.465 

14.38 

4.106 

4.095 

4.098 

4.104 

4.11 

4.108 

4.113 

4.111 

4.101 

4.103 

4.093 

4.098 

4.087 

4.097 

4.077 

4.076 

4.076 

4.072 

4.074 

4.075 

4.072 

4.083 

4.081 

4.082 

4.098 

4.123 

4.119 

4.124 

4.124 

4.094 

4.098 

4.104 

4.093 

4.101 

4.1 

4.097 

4.097 

4.106 

4.106 

4.099 

4.096 

4.101 

4.1 

4.103 

4.071 

4.077 

4.075 

4.073 

4.07 

4.057 

4.053 

4.057 

4.05 

4.055 

4.048 

4.043 

4.031 

4.037 

4.03 

4.09 

1.949 

1.798 

1.759 

1.854 

1.937 

1.909 

1.918 

1.995 

1.866 

2.007 

2.048 

2.309 

1.847 

2.148 

2.178 

2.227 

2.201 

2.127 

2.166 

2.18 

2.155 

2.263 

2.253 

2.1 9 

2.38 

2.492 

2.426 

2.382 

2.437 

2.286 

2.247 

2.314 

2.259 

2.256 

2.27 

2.267 

2.236 

2.404 

2.47 

2.219 

2.417 

2.333 

2.326 

2.206 

2.106 

2.197 

2.127 

2.109 

2.081 

2.041 

1.976 

2.056 

2.012 

2.072 

2.083 

1.937 

1.771 

1.883 

1.856 

2.14 

0.274 

0.288 

0.299 

0.284 

0.251 

0.246 

0.223 

0.214 

0.222 

0.235 

0.274 

0.261 

0.244 

0.247 

0.389 

0.387 

0.392 

0.386 

0.386 

0.4 

0.424 

0.405 

0.397 

0.417 

0.395 

0.329 

0.343 

0.338 

0.328 

0.402 

0.402 

0.397 

0.403 

0.422 

0.406 

0.405 

0.392 

0.394 

0.379 

0.406 

0.388 

0.379 

0.375 

0.393 

0.36 

0.353 

0.367 

0.365 

0.385 

0.399 

0.413 

0.396 

0.418 

0.408 

0.4 

0.385 

0.379 

0.383 

0.385 

0.35 

02-ln 

13.739 

13.756 

NOx-ln 

27.104 

26.95 

CO-In 

37.882 

38.289 

THe-In 

1.32 

1.341 

13.768 26.752 39.693 1.475 

13.761 26.95 39.1 94 1.386 

13.76 27.018 38.333 1.337 

13.768 26.875 39.1 91 1.473 

13.773 26.847 39.739 1.511 

13.766 27.01 38.604 1.405 

13.776 26.912 38.716 1.345 

13.766 27.001 38.914 1.313 

13.78 26.826 39.202 1.378 

13.773 26.865 40.37 1.573 

13.784 26.862 39.48 1.397 

13.773 27.017 39.234 1.311 

13.762 27.12 38.314 1.239 

13.763 27.231 38.224 1.446 

13.766 27.153 38.161 1.375 

13.77 27.149 37.983 1.189 

13.773 27.159 38.242 1.308 

13.776 27.08 38.126 1.369 

13.777 27.065 38.494 1.366 

13.775 27.11 3 38.466 1.311 

13.763 27.286 37.651 1.181 

13.769 27.161 37.782 1.243 

13.76 27.208 38.142 1.233 

13.746 27.345 37.251 1.058 

13.761 27.22 37.407 1.1 26 

13.758 27.083 38.494 1.199 

13.748 27.279 37.513 1.27 

13.747 27.191 37.852 1.277 

13.749 27.16 37.82 1.341 

13.749 27.145 38.137 1.365 

13.744 27.248 37.516 1.282 

13.755 27.084 38.054 1.378 

13.741 27.174 38.146 1.374 

13.756 27.057 38.464 1.394 

13.763 27.067 38.588 1.439 

13.744 27.262 38.266 1.278 

13.738 27.389 36.944 1.119 

13.747 27.242 37.471 1.259 

13.757 27.083 38.553 1.397 

13.754 27.129 38.348 1.331 

13.732 27.326 37.732 1.287 

13.742 27.238 37.566 

13.736 27.395 37.278 

13.722 27.643 35.563 

13.733 27.532 35.75 

13.734 27.582 35.904 

13.747 27.51 36.075 

13.734 27.584 36.084 

13.756 27.373 36.662 

13.738 27.533 36.441 

13.748 27.469 36.331 

13.751 27.408 36.565 

13.731 27.576 36.39 

13.747 27.493 36.357 

1.158 

1.108 

0.959 

0.953 

1.089 

1.091 

1.144 

1.175 

1.105 

0.99 

1.171 

1.236 

1.176 

13.76 27.38536.6921 .163 

13.749 27.422 36.805 1.226 

13.755 27.465 36.29 1.044 

13.757 27.354 37.083 1.056 

13.76 27.20 37.81 

Sentinel Unit 2 50% NOx-NH3-ROG Compliance.xls 

217/2013 

4:18 PM 
Port 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

Average 

Point 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

Oate 

21112013 

2/1 /2013 

2/1/2013 

21112013 

211 /2013 

211 /2013 

2/1 /2013 

21112013 

2/1/2013 

2/1/2013 

211 /2013 

211 /2013 

21112013 

211 /2013 

211/2013 

2/1/2013 

21112013 

211 /2013 

211 /2013 

211 /2013 

2/1/2013 

21112013 

211/2013 

211 12013 

21112013 

211 /2013 

211/2013 

21112013 

211/2013 

211 12013 

211/2013 

211/2013 

211 /2013 

211/2013 

211 12013 

211/2013 

21112013 

2/1/2013 

21112013 

211/2013 

211 /2013 

211 /2013 

21112013 

211 /2013 

211 /2013 

211/2013 

211/2013 

211 /2013 

211/2013 

211/2013 

211 /2013 

211/2013 

211/2013 

21112013 

21112013 

21112013 

211 /2013 

211/2013 

211/2013 

211/2013 

Oeh8AlrQual/lyS8rr1C8S 

1845 N. Case Street 

Orange, California 92865 

714-279-6777 

Time 

15:54 

15:55 

15:56 

15:57 

15:58 

15:59 

16:00 

16:01 

16:02 

16:03 

16:04 

16:05 

16:06 

16:07 

16:08 

16:13 

16:14 

16:15 

16:16 

16:17 

16:18 

16:19 

16:20 

16:21 

16:22 

16:23 

16:24 

16:25 

16:26 

16:27 

16:35 

16:36 

16:37 

16:38 

16:39 

16:40 

16:41 

16:42 

16:43 

16:44 

16:45 

16:46 

16:47 

16:48 

16:49 

16:55 

16:56 

16:57 

16:58 

16:59 

17:00 

17:01 

17:02 

17:03 

17:04 

17:05 

17:06 

17:07 

17:08 

17:09 

REFERENCE METHOD 1-MINUTE AVERAGE DATA 

14.396 4.056 2.033 0.434 

14.389 

14.407 

14.4 

14.412 

14.439 

14.466 

14.474 

14.46 

14.452 

14.453 

14.473 

14.464 

14.501 

14.474 

14.364 

14.367 

14.356 

14.361 

14.349 

14.344 

14.345 

14.343 

14.353 

14.353 

14.317 

14.319 

14.326 

14.318 

14.323 

14.383 

14.367 

14.37 

14.384 

14.4 

14.4 

14.385 

14.37 

14.367 

14.379 

14.347 

14.369 

14.369 

14.365 

14.36 

14.43 

14.435 

14.44 

14.443 

14.439 

14.444 

14.479 

14.462 

14.471 

14.463 

14.456 

14.465 

14.484 

14.481 

14.484 

14.40 

4.062 

4.054 

4.06 

4.056 

4.039 

4.025 

4.02 

4.028 

4.03 

4.027 

4.017 

4.019 

4.003 

4.014 

4.068 

4.068 

4.074 

4.071 

4.079 

4.085 

4.08 

4.084 

4.072 

4.077 

4.106 

4.103 

4.099 

4.104 

4.096 

4.046 

4.053 

4.049 

4.039 

4.028 

4.025 

4.03 

4.04 

4.039 

4.031 

4.049 

4.03 

4.029 

4.03 

4.032 

3.985 

3.981 

3.978 

3.974 

3.978 

3.974 

3.953 

3.959 

3.952 

3.951 

3.953 

3.948 

3.936 

3.936 

3.933 

4.03 

2.236 

1.935 

2.165 

2.096 

1.975 

2.009 

1.981 

2.012 

2.038 

2.074 

2.067 

2.128 

1.96 

1.999 

2.428 

2.253 

2.373 

2.267 

2.331 

2.44 

2.395 

2.381 

2.343 

2.306 

2.389 

2.486 

2.373 

2.402 

2.39 

2.326 

2.394 

2.32 

2.232 

2.309 

2.223 

2.294 

2.31 

2.392 

2.266 

2.369 

2.384 

2.339 

2.333 

2.389 

2.103 

2.071 

2.008 

2.084 

2.158 

2.177 

2.164 

2.129 

2.106 

2.131 

2.035 

2.002 

1.936 

1.945 

1.937 

2.20 

0.392 

0.412 

0.418 

0.423 

0.424 

0.431 

0.445 

0.44 

0.441 

0.437 

0.391 

0.374 

0.396 

0.4 

0.336 

0.345 

0.343 

0.352 

0.342 

0.338 

0.348 

0.335 

0.353 

0.365 

0.329 

0.333 

0.338 

0.325 

0.34 

0.401 

0.387 

0.37 

0.384 

0.392 

0.413 

0.414 

0.4 

0.373 

0.409 

0.379 

0.394 

0.415 

0.388 

0.387 

0.395 

0.4 

0.407 

0.412 

0.422 

0.41 

0.428 

0.444 

0.449 

0.456 

0.446 

0.413 

0.411 

0.402 

0.408 

0.39 

02-ln 

13.75 

13.764 

13.761 

NOx-ln 

27.261 

27.057 

27.094 

CO-In 

37.89 

38.359 

38.81 

THC-In 

1.174 

1.273 

1.324 

13.762 27.066 38.861 1.352 

13.766 27.021 39.447 1.344 

13.769 27.032 39.615 1.256 

13.785 27.007 39.743 1.286 

13.783 27.003 39.802 1.236 

13.764 27.126 39.609 1.299 

13.765 27.127 39.775 1.332 

13.764 27.344 38.172 1.236 

13.761 27.491 37.66 1.1 97 

13.786 27.105 38.802 1.227 

13.764 27.347 39.089 1.301 

13.761 27.574 37.555 1.142 

13.764 27.674 36.426 1.168 

13.76 27.699 36.741 1.129 

13.764 27.547 36.977 1.223 

13.751 27.681 36.628 1.193 

13.742 27.711 36.509 1.08 

13.744 27.783 35.825 0.986 

13.743 27.776 35.943 1.054 

13.761 27.71 35.932 1.143 

13.765 27.458 36.674 1.145 

13.765 27.344 37.616 1.211 

13.765 27.398 37.347 1.176 

13.771 27.403 37.194 1.258 

13.766 27.423 37.223 1.278 

13.77 27.431 36.923 1.105 

13.772 27.575 36.663 1.198 

13.767 27.549 36.971 1.207 

13.774 27.57 36.443 1.246 

13.80427.33437.4881 .354 

13.809 27.239 38.064 1.358 

13.81 27.181 38.667 1.344 

13.794 27.289 38.226 1.252 

13.783 27.383 37.818 1.393 

13.773 27.448 37.199 1.25 

13.793 27.282 37.9 1.305 

13.765 27.506 37.329 1.196 

13.778 27.355 37.432 1.327 

13.777 27.355 37.657 1.292 

13.773 27.38 37.679 1.333 

13.771 27.50537.0791.294 

13.763 27.701 35.826 1.042 

13.779 27.321 37.866 1.366 

13.78527.24938.164 1.271 

13.787 27.218 38.231 1.218 

13.81 27.052 39.247 1.362 

13.785 27.163 38.876 1.36 

13.799 27.17 38.407 1.324 

13.803 27.06 39.26 1.48 

13.795 27.077 39.083 1.325 

13.783 27.135 39.192 1.376 

13.771 27.257 38.655 1.3 

13.765 27.437 37.7 1.255 

13.765 27.313 37.85 1.225 

13.766 27.313 38.072 1.25 

13.766 27.277 38.207 1.251 

13.766 27.251 38.323 1.366 

13.77 27.34 37.88 

Sentinel Unit 2 50% NOx-NH3-AOG Compliance. xis 

217/2013 

4:18 PM 
Port 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

s 

s 

s 

s 

s 

s 

s 

s 

s 

S 

S 

S 

S 

S 

S 

Average 

Point Date 

3 2/1/2013 

3 2/112013 

3 2/1/2013 

3 2/112013 

3 2/112013 

2 2/1/2013 

2 2/1/2013 

2 211/2013 

2 2/112013 

2 2/1/2013 

2/1/2013 

2/1 /2013 

2/1/2013 

2/112013 

2/1/2013 

3 2/1/2013 

3 2/1/2013 

3 211/2013 

3 2/1/2013 

3 2/1/2013 

2 2/1/2013 

2 2/1/2013 

2 2/1/2013 

2 2/112013 

2 2/112013 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

2/1/2013 

211/2013 

2/112013 

2/1/2013 

211/2013 

2/1/2013 

2/112013 

2/1/2013 

2/1/2013 

2/1/2013 

2/1/2013 

211/2013 

2/1/2013 

2/112013 

2/1/2013 

2/112013 

2/112013 

2/112013 

2/1/2013 

2/1/2013 

2/1/2013 

2/1/2013 

211/2013 

2/112013 

2/1/2013 

2/1/2013 

2/1/2013 

2/1/2013 

2111201 3 

211/2013 

211/2013 

211/201 3 

211/2013 

21112013 

211/2013 

88ItaAl,Qual/fY SIlMen 

1845 N. Case Street 

Orange, California 92865 

714-279-6777 

Time 

9:11 

9:12 

9:13 

9:14 

9:15 

9:16 

9:17 

9:18 

9:19 

9:20 

9:21 

9:22 

9:23 

9:24 

9:25 

9:28 

9:29 

9:30 

9:31 

9:32 

9:33 

9:34 

9:35 

9:36 

9:37 

9:38 

9:39 

9:40 

9:41 

9:42 

9:45 

9:46 

9:47 

9:48 

9:49 

9:50 

9:51 

9:52 

9:53 

9:54 

9:55 

9:56 

9:57 

9:59 

10:00 

10:20 

10:21 

10:22 

10:23 

10:24 

10:25 

10:26 

10:27 

10:28 

10:29 

10:30 

10:31 

10:32 

10:33 

10:34 

REFERENCE METHOD 1-MINUTE AVERAGE DATA 

0, 

13.438 

13.45 

13.437 

13.445 

13.45 

13.476 

13.486 

13.492 

13.493 

13.494 

13.482 

13.483 

13.478 

13.468 

13.471 

13.626 

13.624 

13.627 

13.64 

13.63 

13.521 

13.492 

13.497 

13.467 

13.436 

13.427 

13.43 

13.43 

13.427 

13.428 

13.463 

13.473 

13.491 

13.508 

13.497 

13.449 

13.421 

13.414 

13.406 

13.417 

13.424 

13.448 

13.429 

13.422 

16.266 

13.492 

13.493 

13.477 

13.475 

13.478 

13.475 

13.49 

13.488 

13.49 

13.499 

13.487 

13.479 

13.468 

13.473 

13.469 

13.53 

CO, 

4.451 

4.449 

4.455 

4.453 

4.453 

4.445 

4.443 

4.441 

4.444 

4.445 

4.451 

4.454 

4.457 

4.461 

4.461 

4.359 

4.357 

4.356 

4.348 

4.351 

4.419 

4.436 

4.432 

4.449 

4.462 

4.472 

4.471 

4.468 

4.471 

4.471 

4.449 

4.446 

4.435 

4.426 

4.428 

4.462 

4.482 

4.485 

4.491 

4.484 

4.479 

4.463 

4.475 

4.484 

2.879 

4.48 

4.483 

4.489 

4.492 

4.489 

4.488 

4.479 

4.481 

4.481 

4.477 

4.482 

4.488 

4.499 

4.496 

4.497 

4.43 

NO, 

2.847 

2.84 

2.888 

2.772 

2.685 

2.716 

2.825 

2.854 

2.911 

2.886 

2.888 

2.924 

2.885 

2.813 

2.816 

2.788 

2.931 

2.844 

2.71 

2.788 

2.781 

2.83 

2.815 

2.875 

2.883 

2.954 

2.914 

2.866 

2.838 

2.777 

2.886 

2.941 

2.948 

2.939 

2.867 

2.701 

2.874 

2.79 

2.822 

2.836 

2.922 

2.707 

2.859 

2.949 

1.897 

2.594 

2.575 

2.787 

2.623 

2.598 

2.665 

2.649 

2.753 

2.794 

2.802 

2.795 

2.739 

2.748 

2.767 

2.735 

2.80 

CO 

0.765 

0.773 

0.73 

0.713 

0.706 

0.718 

0.763 

0.752 

0.759 

0.746 

0.746 

0.683 

0.636 

0.631 

0.64 

0.601 

0.605 

0.615 

0.627 

0.627 

0.645 

0.677 

0.631 

0.631 

0.642 

0.632 

0.621 

0.622 

0.623 

0.653 

0.488 

0.507 

0.502 

0.475 

0.495 

0.473 

0.409 

0.413 

0.392 

0.403 

0.413 

0.42 

0.416 

0.393 

0.365 

0.733 

0.698 

0.739 

0.681 

0.667 

0.724 

0.707 

0.736 

0.715 

0.702 

0.695 

0.637 

0.527 

0.601 

0.634 

0.62 

02-ln 

13.324 

13.329 

13.318 

13.336 

13.334 

13.339 

13.343 

13.344 

13.345 

13.346 

13.346 

13.346 

13.346 

13.343 

13.345 

13.344 

13.345 

13.345 

13.342 

13.341 

13.344 

13.344 

13.344 

13.345 

13.342 

13.339 

NOx-ln CO-In THC-In 

29.999 51 .869 6.504 

30.002 52.164 6.678 

30.25 49.41 6.1 

30.237 49.472 5.687 

30.261 48.573 5.83 

30.113 49.668 6.007 

29.994 52.707 6.804 

29.966 50.984 6.293 

30.064 50.475 6.219 

30.035 50.274 6.063 

29.968 51.089 6.246 

30.3 49.837 6.137 

30.245 48.1 05 5.758 

30.278 48.08 5.675 

30.385 47.915 5.711 

30.466 46.102 5.278 

30.584 45.441 5.243 

30.37 47.557 5.895 

30.393 46.574 5.445 

30.379 47.29 5.566 

30.225 48.08 5.71 8 

30.216 48.66 5.738 

30.28 47.917 5.623 

30.347 47.854 5.741 

30.353 47.533 5.584 

30.5 48.207 5.823 

13.346 30.396 47.962 5.841 

13.342 30.462 46.927 5.505 

13.343 30.297 48.268 5.912 

13.344 30.268 49.052 6.06 

13.335 30.455 47.93 5.76 

13.344 30.472 46.5 5.431 

13.344 30.486 47.273 5.77 

13.345 30.495 46.707 5.576 

13.342 30.497 47.025 5.484 

13.342 30.504 48.292 5.691 

13.344 3M8 48.838 6.084 

13.333 30.622 46.853 5.745 

13.34 30.669 46.952 5.654 

13.336 30.658 46.727 5.598 

13.345 30.534 46.855 5.524 

13.35 30.379 48.915 5.981 

13.339 30.558 48.111 5.799 

13.331 30.736 47.053 5.65 

13.334 30.703 46.979 5.726 

13.334 30.264 48.649 5.441 

13.331 30.276 47.543 4.97 

13.312 30.44 50.725 6.144 

13.319 30.499 46.567 5.084 

13.322 30.284 47.717 5.544 

13.319 30.268 46.611 4.912 

13.319 30.13 47.982 5.068 

13.325 30.242 47.013 4.774 

13.326 30.208 48.217 5.269 

13.328 30.125 46.092 4.714 

13.329 30.159 46.179 5.027 

13.315 30.429 44.313 4.591 

13.316 30.452 40.961 3.793 

13.318 30.25 46.279 4.94 

13.316 30.342 45.1 57 4.879 

13.34 30.34 47.92 

Sentinel Unit 2 75% NOx-NH3-ROG Compliance.xls 

217/2013 

4:18 PM 
Port 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

5 

S 

S 

S 

S 

s 

s 

S 

S 

S 

s 

S 

S 

S 

S 

Average 

Point 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

Date 

211/2013 

211/2013 

21112013 

21112013 

21112013 

21112013 

211/2013 

211 12013 

211/2013 

211/2013 

211/2013 

211 /2013 

21112013 

21112013 

21112013 

211 /2013 

211 /2013 

211/2013 

211/2013 

21112013 

2/1/2013 

211 12013 

211 /2013 

211 /2013 

211 /2013 

211 /2013 

211/2013 

21112013 

21112013 

211 /2013 

21112013 

21112013 

21112013 

211 /2013 

211 /2013 

2/1/2013 

2/1/2013 

21112013 

21112013 

21112013 

211 /2013 

21112013 

21112013 

211 /2013 

211/2013 

211/2013 

211/2013 

211/2013 

21112013 

21112013 

21112013 

211 12013 

211/2013 

21112013 

211/2013 

2/1/2013 

2/1/2013 

211 12013 

211 /2013 

211/2013 

D.1Ia All qua/flY S.MCIIS 

1845 N. Case Sireel 

Orange, California 92865 

714-279-6777 

REFERENCE METHOD l-MINUTE AVERAGE DATA 

11:06 13.44 4.505 2.647 1.73 

11:07 

11 :08 

11 :09 

11 :10 

11 :11 

11 :12 

11 :13 

11 :14 

11 :15 

11 :16 

11 :17 

11 :1 8 

11 :19 

11:20 

11 :23 

11 :24 

11 :25 

11 :26 

11 :27 

11 :28 

11 :29 

11 :30 

11 :31 

11 :32 

11 :33 

11:34 

11 :35 

11 :36 

11 :37 

11 :43 

11 :44 

11 :45 

11 :46 

11 :47 

11 :48 

11:49 

11 :50 

11 :51 

11 :52 

11 :53 

11 :54 

11 :55 

11 :56 

11 :57 

12:01 

12:02 

12:03 

12:04 

12:05 

12:06 

12:07 

12:08 

12:09 

12:10 

12:11 

12:12 

12:13 

12:14 

12:15 

13.433 

13.432 

13.44 

13.45 

13.441 

13.438 

13.445 

13.452 

13.45 

13.444 

13.437 

13.44 

13.437 

13.438 

13.423 

13.425 

13.418 

13.416 

13.41 

13.406 

13.405 

13.404 

13.407 

13.418 

13.409 

13.405 

13.407 

13.412 

13.413 

13.428 

13.423 

13.422 

13.428 

13.427 

13.43 

13.431 

13.434 

13.429 

13.428 

13.424 

13.417 

13.413 

13.411 

13.407 

13.391 

13.392 

13.401 

13.381 

13.387 

13.382 

13.36 

13.365 

13.378 

13.372 

13.384 

13.381 

13.391 

13.394 

13.39 

13.41 

4.516 

4.519 

4.512 

4.51 

4.515 

4.517 

4.513 

4.513 

4.515 

4.52 

4.524 

4.522 

4.521 

4.521 

4.531 

4.532 

4.537 

4.537 

4.543 

4.545 

4.547 

4.545 

4.541 

4.534 

4.541 

4.543 

4.543 

4.543 

4.543 

4.537 

4.543 

4.546 

4.539 

4.539 

4.539 

4.539 

4.541 

4.543 

4.547 

4.552 

4.561 

4.567 

4.57 

4.571 

4.582 

4.587 

4.583 

4.595 

4.594 

4.602 

4.615 

4.614 

4.61 

4.615 

4.605 

4.608 

4.6 

4.602 

4.608 

4.55 

2.65 

2.754 

2.678 

2.549 

2.666 

2.74 

2.738 

2.719 

2.753 

2.762 

2.703 

2.556 

2.675 

2.731 

2.767 

2.76 

2.836 

2.772 

2.861 

2.893 

2.868 

2.842 

2.815 

2.751 

2.917 

2.667 

2.702 

2.667 

2.734 

2.672 

2.676 

2.609 

2.512 

2.687 

2.646 

2.81 

2.704 

2.808 

2.76 

2.658 

2.651 

2.707 

2.736 

2.667 

2.615 

2.573 

2.548 

2.643 

2.671 

2.784 

2.848 

2.6 

2.622 

2.726 

2.733 

2.862 

2.618 

2.576 

2.724 

2.71 

2.014 

1.639 

1.341 

1.393 

1.715 

1.627 

1.743 

1.627 

1.727 

1.439 

1.539 

1.76 

1.605 

1.488 

1.518 

1.669 

1.564 

1.692 

1.909 

1.693 

1.159 

1.095 

1.273 

1.317 

1.17 

0.945 

1.005 

1.09 

1.152 

1.039 

1.098 

0.949 

0.97 

0.853 

0.848 

0.871 

0.821 

0.812 

0.761 

0.754 

0.662 

0.507 

0.522 

0.497 

0.187 

0.23 

0.217 

0.185 

0.16 

0.183 

0.125 

0.102 

0.129 

0.128 

0.171 

0.145 

0.158 

0.153 

0.147 

0.98 

02·ln NOx-ln CO-In THe-In 

13.308 28.739 107.595 26.957 

13.3 29.032 115.202 30.19 

13.296 29.5 92.548 21 .102 

13.326 29.445 74.547 13.655 

13.322 28.71 94.037 22.019 

13.315 29.232 95.323 20.86 

13.297 28.867 101.647 24.023 

13.323 29.024 100.126 23.144 

13.313 29.298 95.121 21 .555 

13.321 29.22 98.681 22.929 

13.313 29.312 87.169 18.653 

13.3 29.061 99.09 23.474 

13.328 29.128 105.013 24.077 

13.321 29.179 99.934 23.17 

13.318 29.27 99.652 23.815 

13.326 29.051 101 .824 23.389 

13.323 29.085 107.064 25.849 

13.322 28.807 106.946 26.343 

13.318 28.66 112.242 28.279 

13.324 28.553 126.77 33.989 

13.319 29.602 97.873 21.071 

13.311 29.828 78.667 16.033 

13.318 29.477 78.114 15.8 

13.325 29.351 88.364 19.965 

13.323 29.425 92.317 22.339 

13.319 29.804 67.984 11.727 

13.32 29.601 68.443 13.155 

13.318 29.464 70.408 13.872 

13.327 28.981 84.936 19.335 

13.33 29.358 78.027 16.474 

13.318 29.643 66.384 12.494 

13.3 30.182 59.793 9.953 

13.316 30.139 55.33 9.305 

13.318 30.185 56.124 9.505 

13.315 30.395 48.409 6.858 

13.318 30.291 48.56 7.219 

13.322 30.328 46.691 6.857 

13.309 30.457 45.08 6.448 

13.31 30.413 44.597 6.132 

13.315 30.586 42.47 5.524 

13.307 30.513 43.225 5.82 

13.315 30.621 39.274 4.627 

13.309 30.764 33.251 2.752 

13.305 30.707 35.344 3.5 

13.315 30.649 34.69 3.314 

13.3 30.847 23.7 1.135 

13.308 30.822 25.729 1.326 

13.3 31 .002 23.716 1.137 

13.293 31.122 21 .546 0.71 

13.292 31.162 20.933 0.57 

13.291 31 .023 24.653 1.462 

13.27 31.403 21.163 0.672 

13.303 31.075 20.389 0.634 

13.287 31.133 21.551 0.827 

13.278 31.061 22.458 

13.294 31 .108 21 .938 0.779 

13.277 31.323 19.982 0.518 

13.3 31.034 20.528 0.53 

13.297 31.069 20.7 0.606 

13.298 31.146 20.316 0.563 

13.31 29.97 64.24 

Sentinel Unit 2 75% NOx-NH3-ROG Compliance. xis 

217/2013 

4:18 PM 
Port 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

s 

Average 

Point 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

3 

3 

3 

3 

2 

2 

2 

2 

Oate 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

113012013 

DtIII8A1rQuaIIlYSI",clI$ 

1845 N. Case Street 

Orange, California 92865 

714-279-6777 

Time 

11 :02 

11 :03 

11 :04 

11 :05 

11 :06 

11 :07 

11 :06 

11 :09 

11 :10 

11 :11 

11 :12 

11 ;1 3 

11 :14 

11 :15 

11 :16 

11 :27 

11 :26 

11 :29 

11 :30 

11 :31 

11 :32 

11 :33 

11 :34 

11 :35 

11 :36 

11 :37 

11 :36 

11 :39 

11 :40 

11 :41 

11 :46 

11 :47 

11 :46 

11 :49 

11 :50 

11 :51 

11 :52 

11 :53 

11 :54 

11 :55 

11 :56 

11 :57 

11 :56 

11 :59 

12:00 

12:03 

12:04 

12:05 

12:06 

12:09 

12:10 

12:11 

12:12 

12:13 

12:14 

12:15 

12:16 

12:17 

REFERENCE METHOD 1-MINUTE AVERAGE DATA 

13.106 4.644 3.274 3.612 

13.066 

13.091 

13.069 

13.061 

13.074 

13.091 

13.069 

13.092 

13.066 

13.069 

13.094 

13.106 

13.102 

13.093 

13.095 

13.102 

13.11 

13.096 

13.104 

13.091 

13.067 

13.071 

13.061 

13.052 

13.043 

13.017 

13.013 

13.016 

13.006 

13.056 

13.051 

13.061 

13.062 

13.064 

13.06 

13.056 

13.051 

13.033 

13.012 

12.99 

12.962 

12.979 

12.975 

12.956 

12.921 

12.915 

12.922 

12.919 

12.696 

12.905 

12.691 

12.692 

12.697 

12.666 

12.666 

12.661 

12.677 

13.02 

4.65 

4.646 

4.647 

4.653 

4.655 

4.644 

4.643 

4.643 

4.646 

4.644 

4.641 

4.635 

4.636 

4.639 

4.662 

4.663 

4.659 

4.664 

4.657 

4.66 

4.659 

4.667 

4.666 

4.671 

4.67 

4.675 

4.676 

4.665 

4.676 

4.666 

4.666 

4.66 

4.661 

4.657 

4.66 

4.656 

4.656 

4.656 

4.656 

4.667 

4.666 

4.662 

4.661 

4.666 

4.67 

4.673 

4.666 

4.666 

4.679 

4.677 

4.666 

4.667 

4.662 

4.694 

4.691 

4.696 

4.696 

4.66 

3.319 

3.32 

3.371 

3.362 

3.46 

3.522 

3.514 

3.477 

3.5 

3.437 

3.357 

3.262 

3.441 

3.491 

3.259 

3.204 

3.166 

3.246 

3.137 

3.341 

3.321 

3.329 

3.134 

3.203 

3.249 

3.266 

3.246 

3.236 

3.366 

3.231 

3.253 

3.161 

3.247 

3.229 

3.297 

3.332 

3.296 

3.247 

3.334 

3.247 

3.205 

3.24 

3.251 

3.234 

3.096 

3.125 

3.057 

2.957 

3.177 

3. 16 

3.356 

3.105 

3.212 

3.341 

3.154 

3.267 

3.311 

3.27 

3.726 

3.763 

3.791 

3.745 

3.667 

4.063 

3.961 

3.654 

3.902 

3.637 

3.659 

4.022 

4.033 

3.666 

3.134 

3.046 

2.906 

3.027 

3.046 

3.144 

3.003 

2.972 

2.911 

2.699 

2.656 

2.91 

2.635 

2.9 

2.714 

3.247 

3.307 

3.076 

3.09 

3.096 

3.12 

3.173 

3.115 

3.209 

3.172 

3.014 

2.696 

2.662 

2.937 

2.91 6 

2.536 

2.564 

2.602 

2.606 

2.046 

2.174 

2.166 

2.153 

2.204 

2.1 14 

2.1 39 

2.035 

2.127 

3.05 

02-ln NOx-ln 

13.027 31.705 121.99 22.93 

13.006 31.706 119.331 21.613 

13.007 31.46 120.927 22.063 

13.001 31 .373 121 .192 22.366 

12.99 31.476 120.661 22.422 

12.977 31.524 120.006 21 .726 

12.991 31.399 123.032 23.153 

12.967 31.626 116.207 21 .646 

12.966 31.601 116.526 20.969 

12.963 31 .796 116.133 21 .505 

12.966 31.692 116.336 21 .107 

12.997 31.454 122.614 22.607 

12.996 31.196 126.066 24.119 

12.995 31.364 130.774 25.41 

12.993 31 .744 116.054 21 .614 

12.994 32.607 11 1.621 20.053 

13 32.651 110.02 19.719 

13.009 32.636 105.023 16.399 

12.996 32.503 109.341 19.641 

13.009 32.296 109.762 16.663 

13.002 32.366 11 3.377 20.54 

12.977 32.592 106.65 19.059 

12.956 32.674 110.151 20.006 

12.951 32.705 107.414 16.22 

12.942 32.65 106.426 16.771 

12.931 32.622 106.013 16.761 

12.925 32.666 106.304 16.456 

12.919 32.766 107.666 16.766 

12.923 32.576 106.246 19.073 

12.912 32.694 102.1 95 17.493 

12.939 32.616 111.534 19.941 

12.939 32.492 113.034 20.464 

12.946 32.497 107.914 19.093 

12.95 32.663 107.236 19.173 

12.956 32.713 105.445 16.161 

12.944 32.671 105.6 16.195 

12.935 32.913 104.66 17.421 

12.93 32.902 103.726 17.625 

12.92 32.74 105.601 16.613 

12.915 32.677 104.199 17.612 

12.693 32.929 104.464 17.459 

12.663 33.056 104.353 17.503 

12.666 33.056 101.123 17.166 

12.675 32.916 105.176 16.274 

12.65 32.996 103.649 17.661 

12.626 33.256 97.522 16.402 

12.621 33.096 100.253 16.66 

12.62 33.066 99.925 17.316 

12.621 32.656 99.669 17.257 

12.606 33.217 95.1 03 15.904 

12.613 32.936 96.956 15.943 

12.791 33.39 97.446 16.294 

12.797 33.025 96.209 15.966 

12.769 33.006 96.901 17.067 

12.763 33.27 93.463 15.104 

12.769 32.926 97.263 16.246 

12.761 33.51 94.062 15.365 

12.757 33.333 95.644 15.426 

12.92 32.52 106.31 

Sentinel Unit 2100% NOx-NH3·ROG Compliance. xis 

217/2013 

4:19 PM 
Port 

5 

S 

S 

S 

s 

s 

s 

s 

s 

s 

S 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

E 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

N 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

w 

Average 

Point 

3 

3 

3 

3 

2 

2 

2 

3 

3 

3 

3 

2 

2 

2 

3 

3 

3 

3 

2 

2 

2 

3 

3 

3 

3 

3 

2 

2 

2 

2 

2 

Date 

1/3012013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1130/2013 

1/30/2013 

113012013 

1130/2013 

1/30/2013 

1/30/2013 

1/3012013 

113012013 

113012013 

1130/2013 

1130/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1130/2013 

1130/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/3012013 

1/3012013 

1/3012013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

113012013 

1/30/2013 

1/30/2013 

1/30/2013 

1/30/2013 

113012013 

D,I18A1,QualllY S,rrlC6I 

1845 N. Case Sireel 

Orange, California 92865 

714-279-6777 

Time 

13:12 

13:13 

13:14 

13:15 

13:18 

13:19 

13:20 

13:23 

13:24 

13:25 

13:26 

13:31 

13:32 

13:33 

13:34 

13:37 

13:38 

13:39 

13:42 

13:43 

13:44 

13:45 

14:29 

14:30 

14:31 

14:32 

14:35 

14:36 

14:37 

14:40 

14:41 

14:42 

14:43 

14:51 

14:52 

14:53 

14:54 

14:55 

14:56 

14:57 

14:58 

14:59 

15:00 

15:01 

15:02 

15:03 

15:04 

15:05 

REFERENCE METHOD 1-MINUTE AVERAGE DATA 

12.873 4.763 2.976 2.529 

12.879 

12.862 

12.872 

12.868 

12.868 

12.863 

12.886 

12.882 

12.868 

12.88 

12.886 

12.889 

12.891 

12.886 

12.895 

12.911 

12.915 

12.923 

12.921 

12.925 

12.918 

12.95 

12.95 

12.958 

12.96 

12.969 

12.984 

12.979 

12.98 

12.974 

12.973 

12.969 

12.979 

12.981 

12.981 

12.978 

12.98 

12.989 

12.983 

12.979 

12.982 

12.993 

12.994 

12.996 

12.993 

12.996 

12.996 

12.93 

4.762 

4.775 

4.772 

4 .782 

4.764 

4.787 

4.776 

4.764 

4.795 

4.789 

4.795 

4.787 

4.789 

4.795 

4.792 

4.783 

4.784 

4.783 

4.785 

4.782 

4.789 

4.806 

4.809 

4.806 

4.806 

4.805 

4.798 

4.804 

4.807 

4.812 

4.815 

4.82 

4.819 

4.819 

4.818 

4.822 

4.822 

4.816 

4.823 

4.823 

4.823 

4.817 

4.817 

4.816 

4.819 

4.816 

4.816 

4.80 

2.896 

3.032 

2.989 

2.969 

3.001 

3.089 

3.113 

2.967 

2.975 

2.984 

3.135 

3.089 

3.16 

3.134 

3.082 

3.059 

3.088 

2.95 

2.987 

2.939 

2.914 

2.83 

2.868 

2.797 

2.903 

2.896 

2.774 

2.871 

2.787 

2.849 

2.771 

2.829 

2.953 

2.919 

2.864 

2.989 

2.951 

3.051 

3.053 

3.103 

3.167 

3.017 

2.993 

3.036 

2.969 

2.95 

3.039 

2.97 

2.642 

2.486 

2.645 

2.1 

2.227 

2.242 

2.232 

2.292 

2.111 

2.213 

2.83 

2.943 

2.679 

2.982 

2.943 

3.034 

2.734 

3.031 

2.837 

3.068 

2.931 

1.951 

2.089 

1.881 

1.979 

1.769 

1.77 

1.796 

1.684 

1.668 

1.656 

1.927 

1.697 

1.816 

1.785 

1.713 

1.768 

1.988 

1.815 

1.926 

1.839 

1.741 

1.762 

1.791 

1.632 

1.621 

2.22 

02-ln 

12.757 

12.758 

NOx-ln 

33.806 

33.647 

CO-In 

90.76 

92.728 

THC-In 

14.408 

14.825 

12.752 34.016 88.842 12.945 

12.754 33.869 93.807 14.6 

12.773 33.7 92.09 14.647 

12.775 33.41 98.843 16.63 

12.777 33.524 97.093 14.989 

12.79 33.682 97.675 16.075 

12.803 33.554 102.762 16.603 

12.797 33.865 99.041 16.349 

12.803 33.626 100.764 16.627 

12.777 34.627 90.333 14.122 

12.789 34.659 93.374 14.561 

12.802 34.718 83.801 12.296 

12.79 34.478 93.158 14 .967 

12.801 34.261 92.283 14.664 

12.817 34.203 94.009 14.4 

12.815 34.436 84.498 12.663 

12.832 33.819 97.343 15.782 

12.839 34.014 93.227 14.428 

12.838 33.834 101 .378 16.594 

12.832 34.1 01 96.702 15.289 

12.869 34.653 71 .963 10.735 

12.873 34.81 74.991 11 .895 

12.873 34.64 68.522 9.369 

12.888 34.47 75.477 11.402 

12.887 34.77 8.663 

12.915 34.468 60.818 7.968 

12.903 34.735 60.686 8.095 

12.903 34.494 62.488 8.242 

12.888 34.852 59.106 7.514 

12.883 34.813 57.773 7.073 

12.885 34.932 57.922 7.362 

12.884 34.814 63.811 8.915 

12.878 34.995 55.375 6.724 

12.877 34.805 57.066 6.975 

12.882 34.927 55.592 7.097 

12.877 35.139 54.355 6.65 

12.895 34.839 53.057 6 .01 

12.878 34.931 58.171 7.316 

12.877 34.986 53.845 6.177 

12.88 35.043 56.125 6.823 

12.904 34.966 55.121 6.914 

12.906 34.808 55.775 6.618 

12.894 34.839 54.248 5.966 

12.891 35.099 54.214 6.572 

12.903 34.782 56.66 7.1 

12.901 34.995 53.572 6.688 

12.84 34.40 77.00 

Sentinel Unit 2100% NOx-NH3-ROG Compliance. xis 

217/2013 

4:19PM 
Appendix C.2.3 One Minute Data Logger Data 

R0410673 C-6 
Date 

1/30/2013 

1/30/2013 

1/30/2013 

1/ 30/ 2013 

1/ 30/ 2013 

1/ 30/ 2013 

1/ 30/ 2013 

1/ 30/ 2013 

1/30/2013 

1/30/2013 

1/30/2013 

1/ 30/2013 

1/ 30/ 2013 

1/ 30/ 2013 

1/ 30/ 2013 

~ ~ N~ W ~ N~ 

Time % % PPM PPM % PPM 

7:19:00 0.148 0.237 -0.007 -0.431 0.044 0.177 

7:20:00 0.123 0.091 -0.001 -0.268 0.042 0.194 

7:21:00 0.119 -0.01 -0.004 0.007 0.039 0.189 

7:22:00 ~0i;-:;.,11;,:,8_--;0:-;0;:;1.;.6+...,0;-0;,0;;;1-t-i;0-;:0:i;05;-~0i;-'0i::3;::7,..., 0.192 

7:23:00 L...0;~1;;:16:-_-O;.:::0;,23;:,..J 3.724 0.008 0.038 3.483 

7:24:00 8.783 4.706 4.822 1.623 6.427 4.876 

7:25:00 19.243 9.66 4.822 9.224 19.315 4.868 

7:26:00 18.966 9.654 4.817 9.56 18.96 4.867 

7:27:00 18967 9 65 4 824 9 522 18959 4.881 

7:28:00 4.889 

7:29:00 1.903 

7:30:00 0.26 

7:31:00 10.118 5.028 0.063 7.835 10.087 0.261 

7:32:00 10.108 5.022 3.557 4.54 10.071 0.257 

7:33:00 '"I -:1"0;,: .1;04:-....;;5".0,;.19:---=3;.;.7;;;3;;4---,4-:.4"'95,.....--=1"0".0"'7"'"' 0.251 

1/ 30/2013 7:34:00 10.078 5.021 2.688 4.506 7.608 0.376 

1/30/2013 7:35:00 10.06 5.022 0.Q15 4.492 0.Q78 0.522 

1/30/2013 7:36:00 10.058 5.019 0.006 4.461 0.036 0.521 

1/30/2013 7:37:00 10.051 5.016 0.005 4.44 0.023 1.001 

1/ 30/2013 7:38:00 10.052 5.01 0.006 4.42 0.022 2.525 

1/ 30/ 2013 7:39:00 10.053 5.008 0.009 4.391 0.527 0.206 

1/ 30/ 2013 7:40:00 10.054 5.004 0.003 4.384 0.019 0.047 

1/ 30/ 2013 7:41:00 10.058 5 0.368 4.348 0.02 0.061 

1/ 30/ 2013 7:42:00 10.06 4.996 4.854 4.327 0.0 22 0.051 

1/30/2013 7:43:00 10.063 4.991 4.812 4.312 9.929 0.051 

1/30/2013 7:44:00 10.068 4.987 4.447 4.293 20.886 2.001 

1/30/2013 7:45:00 10.071 4.982 3.035 4.264 20.909 4.725 

1/30/2013 7:46:00 10.079 4.977 2.584 4.245 20.909 4.817 

1/ 30/ 2013 7:47:00 10.087 4.974 2.563 4.226 20.909 4.858 

1/ 30/ 2013 7:48:00 10.095 4.967 2.445 4.206 20.908 4.868 

1/ 30/ 2013 7:49:00 10.098 4.961 0.879 4.189 20.908 1.379 

1/ 30/ 2013 7:50:00 10.106 4.955 0.4 4.161 20.907 0.076 

1/30/2013 7:51:00 10.108 4.947 0.297 4.132 20.907 2.614 

1/30/2013 7:52:00 10.115 4.94 0.277 4.117 20.907 3.805 

1/30/2013 7:53:00 10.121 4.931 0.251 4.085 20.865 0.926 

1/30/2013 7:54:00 10.128 4.922 0.234 4.069 20.857 0.063 

W THe 

PPM PPM 

-0.234 0.844 

-0.12 0.85 N2/NOx Mode 

0.163 0.878 

0.154 1.183 NO/ NO Mode 

0.159 -0.649 Cal Zero 

1.549 0.003 

186.631 I 0.011 ITHe Zefo;NO/ NO, Mode 

245.437 0.013 

244.606 45.104 

239.82 83.368 NO/NO Mode 

I 240.102 I 83.584 Cat High 

239.924 83.659 N02/ NO Mode 

135.45 84.321 

136.159 85.12 THe High 

""'13:';6"'.9;;;5;;;5+-:8;';5;;;.0;:';1;"3 .JN02/ NO, Mode; Mid 

119.951 50.231 

7.43 46.946 

0.13 46.84 N02/NO Mode 

0.12 46.827 

0.12 46.809 ITHC Mid 

0.112 41.305 

0.114 25.588 NOx Cal Zero 

0.113 25.493 N2/ NO, Mode 

0.117 25.4 ITHC Low 

0.138 22.827 NO, Cat High; N2/ NO Mode 

0.393 2.682 

0.425 2.368 

0.424 2.228 NO/NO, Mode 

0.426 2.269 NO, Mid 

0.373 2.251 NO/ NO Mode 

0.362 2.163 

0.358 2.417 N02/NO Mode 

0.388 2.569 

0.412 2.503 N02/NO, Mode 

0.31 2.499 

0.35 2.481 NOx Cal Zero 

1/ 30/ 2013 7:55:00 10.134 4.911 0.238 4.049 19.949 12.465 17.961 10.595 

78.895 

19.631 

1/ 30/ 2013 7:56:00 10.144 4.902 0.215 4.027 16.314 46.049 426.311 

1/ 30/ 2013 7:57:00 10. 144 4.894 0.296 3.999 16.485 48.268 107.835 

1/ 30/ 2013 7:58:00 10.144 4.886 0.302 3.996 16.491 48.422 75.577 

1/30/2013 7:59:00 10.144 4.879 0.354 3.969 16.489 16.447 76.336 

1/30/2013 8:00:00 10.144 4.87 0.363 3.948 16.495 22.89 77.537 

1/30/2013 8:01:00 10.15 4.864 0.239 3.942 15.67 24.229 54.812 

1/30/2013 8:02:00 10.204 4.856 0.136 3.911 14.429 24.351 1181.994 

1/ 30/ 2013 8:03:00 13.479 0.606 0.054 3.437 13.408 24.327 416.549 

1/ 30/ 2013 8:04:00 20.615 0.012 0.027 0.861 12.953 45.523 23.077 

1/ 30/ 2013 8:05:00 20.655 0.007 0.029 0.311 12.89 47.436 6.214 

1/ 30/ 2013 8:06:00 20.669 0.006 0.017 0.316 12.937 48.839 5.759 

1/ 30/ 2013 8:07:00 20.682 0.006 0.009 0.254 12.835 44.136 6.595 

1/30/2013 8:08:00 20.622 0.008 0.006 0.265 12.886 44.211 6.213 

1/30/2013 8:09:00 10.229 4.573 0.001 0.178 10.527 6.886 3.529 

1/30/2013 8:10:00 9.993 5.04 -0.006 -0.288 9.927 0.389 -0.207 

1/ 30/2013 8:11:00 1,....;9;.;.9;;8"'3--;5;;;.0;,48::---0;;;.;;:00;;;2;.., -0.321 9.927 0.276 -0.215 

1/ 30/ 2013 8:12:00 3.273 1.425 3.117 -0.096 5.325 11.443 0.162 

1/ 30/ 2013 8:13:00 0.149 -0.004 4.761 0.226 0.046 24.548 0.262 

1/ 30/ 2013 8:14:00 1~0i;-~12;:;7---;-0:-;.00~5-...,4:"7;;6,;7--i;0..,;2~54::-~0;-0;;,1;':'6--2~4~.5;';5:::8-""0i;-1~44;7-, 

1/ 30/ 2013 8:15:00 0.127 -0.005 2.348 1.509 0.014 12.531 27.324 

1/ 30/2013 8:16:00 0.126 -0.003 -0.004 4.412 0.009 0.185 133.067 

4.433 NOx Cal High 

4.069 

3.97 

2.292 

40.585 NOx Mid 

87.3 

3.133 

1.259 

0.838 

0.786 

0.64 

0.428 

0.101 

0.02 02 bias 

0.068 

-0.012 

-0.012 NOx bias 

-0.011 

-0.007 
0, 

% 

CO2 NO~ CO O2 NO, CO THC 

Date Time % PPM PPM % PPM PPM PPM 

1/30/2013 8:17:00 

1/30/2013 8:18:00 

1/30/2013 8:19:00 

1/30/2013 8:20:00 

1/30/2013 8:21:00 

1/30/2013 8:22:00 

1/30/2013 8:23:00 

1/30/2013 8:24:00 

1/30/2013 8:25:00 

1/30/2013 8:26:00 

1/30/2013 8:27:00 

1/30/2013 8:28:00 

1/30/2013 8:29:00 

1/30/2013 8:30:00 

1/30/2013 8:31:00 

1/30/2013 8:32:00 

1/30/2013 8:33:00 

1/30/2013 8:34:00 

1/30/2013 8:35:00 

1/30/2013 8:36:00 

1/30/2013 8:37:00 

1/30/2013 8:38:00 

1/30/2013 8:39:00 

1/30/2013 8:40:00 

1/30/2013 8:41:00 

1/30/2013 8:42:00 

1/30/2013 8:43:00 

1/30/2013 8:44:00 

1/30/2013 8:45:00 

1/30/2013 8:46:00 

1/30/2013 8:47:00 

1/ 30/2013 8:48:00 

1/30/2013 8:49:00 

1/30/2013 8:50:00 

1/30/2013 8:51:00 

1/30/2013 8:52:00 

1/30/2013 8:53:00 

1/30/2013 8:54:00 

1/30/2013 8:55:00 

1/30/2013 8:56:00 

1/30/2013 8:57:00 

1/30/2013 8:58:00 

1/30/2013 8:59:00 

1/30/2013 9:00:00 

1/30/2013 9:01:00 

1/30/2013 9:02:00 

1/30/2013 9:03:00 

1/30/2013 9:04:00 

1/30/2013 9:05:00 

1/30/2013 9:06:00 

1/30/2013 9:07:00 

1/30/2013 9:08:00 

1/30/2013 9:09:00 

0.126 

10.677 

20.58 

20.607 

20.613 

20.606 

20.621 

20.628 

20.641 

20.651 

20.656 

20.279 

13.667 

13.525 

13.517 

13.512 

13.53 

13.528 

13.558 

13.558 

17.395 

17.309 

13.481 

13.477 

13.467 

13.479 

13.456 

13.43 

13.075 

17.19 

13.111 

13.065 

13.075 

13.08 

13.078 

13.077 

13.085 

17.945 

17.753 

13.096 

13.09 

13.084 

13.093 

13.084 

13.074 

13.072 

13.08 

16.059 

20.719 

19.863 

0.628 

0.147 

0.124 

o -0.001 4.546 0.011 0.14 I 136.439 I -0.007 CO bias 

0.023 -0.002 3.35 8.777 23.792 105.568 

0.043 0.022 0.379 14.177 23.313 53.357 

0.045 0.018 0.235 13.33 30.26 42.322 

0.047 0.D35 0.241 12.74 39.91 22.294 

0.05 0.034 0.242 12.768 41.27 7.437 

0.052 0.006 0.243 12.799 41.259 7.192 

0.054 0.014 0.231 12.874 40.541 7.445 

0.056 0.005 0.228 12.942 38.997 8.36 

0.058 0.003 0.22 12.963 37.848 9.584 

0.06 0.005 0.211 12.968 38.011 10.17 

0.347 0.052 0.224 12.972 38.479 9.426 

4.212 1.543 0.067 12.969 38.86 9.13 

4.232 1.596 0.092 12.97 38.924 8.989 

4.241 1.588 0.093 12.961 38.686 9.007 

4.249 1.553 0.144 12.961 37.294 9.975 

4.24 1.582 0.167 12.962 36.577 11.492 

4.246 1.657 0.184 12.962 36.694 11.541 

4.234 1.644 0.198 12.968 36.602 ll.419 

4.238 1.681 0.193 12.96 36.804 10.95 

1.882 0.817 0.192 12.963 36.775 10.923 

2.178 0.775 0.163 12.964 36.674 10.983 

4.292 1.759 0.177 12.959 36.785 11.129 

4.294 1.782 0.163 12.961 36.708 10.835 

4.296 1.816 0.193 12.962 36.67 11.57 

4.29 1.814 0.226 12.962 36.597 11.562 

4.299 1.786 0.811 12.955 33.904 30.107 

4.315 1.872 2.396 12.964 31.932 84.183 

4.534 1.944 1.121 12.95 36.574 42.257 

2.099 0.935 0.204 12.949 36.168 13.295 

4.532 2.08 1.177 12.96 33.209 45.589 

4.536 2.271 1.94 12.96 32.751 73.851 

4.534 2.273 1.846 12.961 32.891 70.347 

4.533 2.346 1.912 12.968 32.922 69.71 

4.538 2.386 1.723 12.963 33.202 66.195 

4.538 2.272 1.69 12.977 33.105 66.22 

4.535 2.266 1.628 12.989 32.955 66.892 

1.564 0.905 1.141 12.98 33.094 66.07 

1.948 0.803 0.413 12.98 33.097 65.946 

4.536 2.376 1.337 12.974 33.423 64.144 

4.536 2.314 1.228 12.977 33.663 56.081 

4.54 2.343 1.118 12.98 33.781 56.524 

4.537 2.394 0.693 12.986 34.226 41.641 

4.546 2.4 0.604 12.983 34.339 38.9 

4.551 2.517 0.605 12.99 33.802 45.454 

4.553 2.529 0.568 12.978 34.279 46.105 

4.55 2.599 0.421 12.983 34.308 36.172 

2.684 1.717 0.37 12.981 34.448 34.277 

0.101 0.015 0.219 12.978 34.484 34.458 

0.111 0.012 0.257 11.84 33.319 30.49 

0.055 0.006 3.414 0.179 1.295 102.896 

0.051 0.003 4.496 0.026 0.452 136.686 

0.049 0.001 4.507 0.007 0.316 136.62 

1/30/2013 9:10:00 4.811 2.62 -0.006 3.233 5.972 0.933 101.55 

1/30/2013 9:11:00 9.991 5.122 -0.002 -0.146 9.919 0.271 2.538 

1/ 30/2013 9:12:00 "1-:;10":'.0;;;1;--':;5c;.1;'::3~2-"";'''0=' -0.339 9.923 0.246 -0.24 

1/30/2013 9:13:00 7.943 3.928 0.835 -0.299 6.901 6.013 -0.244 

1/30/2013 9:14:00 "1-;;'0.~17;;5"""'-;0;';.0;;;6~9--4~~74;;5"""'--;O~.1:;;0-i'1--0;':'.~04~4;-"";24:;'.~38;';6"""'-:::-0.';:;02:::6"'" 

1/30/2013 9:15:00 0.123 0.057 4.759 0.21 0.01 24.443 0.128 

0.057 

5.151 

2.468 

2.155 

0.214 

0.161 

0.26 

0.244 

0.299 

0.32 

0.29 

0.298 

0.318 Start Strat 

0.361 

0.227 

0.334 

0.359 

0.451 

0.309 

0.279 

0.329 

0.317 

0.258 

0.362 

0.352 

2.696 

13.51 

6.713 

0.452 

5.173 

11.474 

10.674 

10.331 

9.615 

9.632 

9.727 

9.606 

9.622 

9.36 

7.216 

7.553 

4.521 

4.103 

5.082 

5.805 

3.501 

3.335 

3.173 

2.776 

0.687 

-0.007 

-0.007 CO bias 

0.021 

-0.014 

-0.014 02/C02 bias 

-0.015 

-0.014 NOx bias 

-0.014 
Date Time 

1/30/2013 9:16:00 

1/30/2013 9:17:00 

1/30/2013 9:18:00 

1/30/2013 9:19:00 

1/ 30/ 2013 9:20:00 

1/30/ 2013 9:21:00 

1/ 30/ 2013 9:22:00 

1/30/2013 9:23:00 

1/30/2013 9:24:00 

1/30/2013 9:25:00 

1/30/2013 9:26:00 

1/30/2013 9:27:00 

1/ 30/2013 9:28:00 

1/ 30/ 2013 9:29:00 

1/30/ 2013 9:30:00 

1/30/2013 9:31:00 

1/30/2013 9:32:00 

1/30/2013 9:33:00 

1/30/2013 9:34:00 

1/30/2013 9:35:00 

1/30/2013 9:36:00 

1/ 30/2013 9:37:00 

1/30/2013 9:38:00 

1/30/2013 9:39:00 

1/30/2013 9:40:00 

1/30/2013 9:41:00 

1/30/2013 9:42:00 

1/30/2013 9:43:00 

1/30/2013 9:44:00 

1/30/2013 9:45:00 

1/ 30/ 2013 9:46:00 

1/ 30/ 2013 9:47:00 

1/30/2013 9:48:00 

1/30/2013 9:49:00 

1/30/2013 9:50:00 

1/30/2013 9:51:00 

1/30/2013 9:52:00 

1/ 30/2013 9:53:00 

1/ 30/2013 9:54:00 

1/ 30/2013 9:55:00 

1/30/2013 9:56:00 

1/30/2013 9:57:00 

1/30/2013 9:58:00 

1/30/2013 9:59:00 

1/30/2013 10:00:00 

1/30/2013 10:01:00 

1/ 30/2013 10:02:00 

1/30/ 2013 10:03:00 

1/30/2013 10:04:00 

1/30/2013 10:05:00 

1/30/2013 10:06:00 

1/30/2013 10:07:00 

1/30/2013 10:08:00 

1/30/2013 10:09:00 

1/ 30/2013 10:10:00 

1/ 30/ 2013 10:11:00 

1/ 30/2013 10:12:00 

1/30/2013 10:13:00 

1/30/2013 10:14:00 

0, 

% 

0.123 

0.122 

14.836 

20.724 

20.752 

20.748 

20.756 

20.761 

20.723 

20.757 

20.731 

20.721 

20.404 

13.276 

13.104 

13.103 

13.106 

13.103 

13.082 

13.082 

13.083 

13.08 

13.073 

13.057 

13.061 

13.057 

13.057 

13.057 

13.05 

13.054 

13.055 

13.048 

13.056 

13.04 

13.052 

13.037 

13.037 

13.03 

13.044 

13.044 

13.056 

13.063 

13.079 

13.077 

13.1 

13.114 

13.119 

13.126 

13.139 

13.133 

13.127 

13.113 

13.118 

13.086 

13.06 

13.054 

13.051 

13.036 

13.019 

CO, 

% 

0.053 

0.051 

0.079 

0.087 

0.088 

0.091 

0.089 

0.089 

0.106 

0.09 

0.102 

0.109 

0.341 

4.529 

4.543 

4.544 

4.542 

4.544 

4.552 

4.554 

4.552 

4.555 

4.56 

4.568 

4.563 

4.566 

4.566 

4.565 

4.571 

4.567 

4.563 

4.565 

4.559 

4.565 

4.559 

4.566 

4.566 

4.568 

4.565 

4.569 

4.567 

4.571 

4.57 

4.579 

4.575 

4.574 

4.577 

4.58 

4.576 

4.578 

4.578 

4.583 

4.576 

4.589 

4.6 

4.6 

4.6 

4.604 

4.606 

NO, 

PPM 

4.766 

4.764 

1.443 

0.012 

0.01 

0.009 

0.002 

0.007 

0.017 

0.01 

0.017 

0.021 

0.074 

3.078 

3.114 

3.148 

3.022 

2.974 

3.04 

3.092 

3.054 

2.996 

3.144 

3.156 

3.06 

3.068 

3.067 

3.233 

3.257 

3.198 

3.234 

3.227 

3.135 

3.202 

3.089 

3.157 

3.168 

3.16 

3.061 

3.125 

3.064 

3.158 

3.006 

3.241 

3.303 

3.17 

3.224 

3.245 

3.208 

3.11 

3.159 

3.142 

3.028 

3.009 

3.356 

3.374 

3.386 

3.419 

3.449 

co 

PPM 

0.224 

0.224 

0.218 

0.206 

0.258 

0.221 

0.195 

0.198 

0.204 

0.209 

0 .2 

0.198 

0.202 

0.086 

0.099 

0.088 

0.131 

0.15 

0.144 

0.206 

0.272 

0.317 

0.274 

0 .238 

0.232 

0.244 

0.225 

0.253 

0.226 

0.203 

0.207 

0.196 

0.27 

0.23 

0.278 

0.308 

0.45 

0.518 

0.564 

0.655 

0.668 

0.521 

0.564 

0.579 

0.492 

0.445 

0.55 

0.495 

0.51 

0.604 

0.497 

0.512 

0.712 

3.37 

4.229 

4.223 

4.193 

4.128 

4.087 

0 , 

% 

0.009 

0.009 

10.284 

12.95 

12.938 

12.953 

12.947 

12.953 

12.94 

12.949 

12.954 

12.952 

12.953 

12.952 

12.955 

12.954 

12.957 

12.956 

12.953 

12.954 

12.955 

12.951 

12.936 

12.906 

12.931 

12.939 

12.93 

12.925 

12.914 

12.921 

12.931 

12.926 

12.925 

12.929 

12.938 

12.927 

12.939 

12.924 

12.944 

12.946 

12.96 

12.966 

12.973 

12.97 

12.991 

12.993 

13.003 

13.007 

13.012 

13.015 

13.004 

12.992 

12.997 

12.982 

12.958 

12.952 

12.949 

12.94 

12.921 

NO, 

PPM 

24.45 

24.455 

31.398 

34.443 

35.272 

35.373 

35.46 

35.396 

35.633 

35.597 

35.637 

35.496 

35.796 

36.109 

36.156 

36.127 

35.718 

35.637 

35.804 

35.697 

35.455 

35.482 

35.562 

36.065 

35.886 

35.886 

35.812 

35.873 

36.128 

36.165 

36.073 

36.04 

35.793 

35.871 

35.647 

35.702 

35.549 

35.376 

35.151 

35.181 

34.953 

35.209 

35.005 

35.248 

35.258 

35.301 

35.51 

35.667 

35.542 

35.367 

35.499 

35.547 

34.289 

30.813 

30.639 

30.96 

31.015 

31.063 

31.127 

co 

PPM 

0.127 

0.129 

12.904 

27.183 

18.418 

16.218 

15.764 

15.915 

15.429 

14.409 

14.315 

14.616 

14.031 

12.097 

11.086 

10.942 

11.975 

13.461 

13.953 

14.758 

17.105 

17.601 

18.189 

16.019 

15.454 

15.714 

15.708 

15.844 

14.927 

14.58 

14.423 

14.343 

15.949 

15.96 

17.066 

18.854 

21.377 

23.35 

25.873 

26.879 

28.259 

25.257 

24.967 

25.01 

24.118 

23.857 

24.731 

24.558 

24.892 

28.009 

25.414 

25.595 

29.34 

115.434 

145.171 

146.8 

144.37 

142.425 

140.12 

THC 

PPM 

-0.014 

-0.Dl5 

1.074 

2.503 

1.013 

0.737 

0 .631 

0.599 

0.555 

0.5 

0.559 

0.532 

0.434 

0.384 

0.287 

0.273 

0.34 

0.281 

0.422 

0.563 

0.687 

0.591 

0.809 

0.657 

0.548 

0.549 

0.592 

0.544 

0.471 

0.522 

0.421 

0.413 

0.571 

0.588 

0.666 

0.72 

1.085 

1.301 

1.584 

1.626 

1.644 

1.405 

1.298 

1.453 

1.35 

1.285 

1.411 

1.448 

1.419 

1.879 

1.369 

1.599 

1.672 

20.991 

29.835 

30.479 

29.279 

28.461 

27.835 
~ ~ N~ 00 ~ N~ 00 

Date Time % % PPM PPM % PPM PPM 

1/ 30/ 2013 10:15:00 13.04 4.601 3.385 4.003 12.946 31.081 138.731 

1/ 30/ 2013 10:16:00 13.046 4.603 3.419 4.025 12.949 31.419 137.494 

1/ 30/ 2013 10:17:00 13.058 4.612 3.391 3.954 12.962 31.677 138.223 

1/30/2013 10:18:00 13.097 4.611 3.29 4.097 13.003 31.494 141.094 

1/30/2013 10:19:00 13.118 4.614 3.32 4.063 13.029 31.473 139.47 

1/ 30/ 2013 10:20:00 13.125 4.626 3.343 4.097 13.042 31.644 141.301 

1/ 30/ 2013 10:21:00 13.138 4.629 3.383 4.002 13.062 31.793 136.38 

1/ 30/ 2013 10:22:00 13.14 4.636 3.226 3.947 13.065 31.746 134.307 

1/30/ 2013 10:23:00 13.143 4.639 3.217 4.082 13.081 31.634 139.179 

1/30/2013 10:24:00 13.151 4.638 3.246 4.134 13.084 31.693 140.094 

1/30/2013 10:25:00 13.16 4.637 3.328 4.175 13.088 31.719 144.857 

1/ 30/ 2013 10:26:00 13.175 4.638 3.403 4.305 13.112 31.541 147.861 

1/ 30/ 2013 10:27:00 13.173 4.645 3.505 4.209 13.108 32.039 143.433 

1/ 30/ 2013 10:28:00 13.186 4.643 3.367 3.906 13.126 32.27 132.489 

1/30/2013 10:29:00 13.192 4.646 3.335 3.968 13.136 32.113 133.851 

1/30/2013 10:30:00 13.204 4.643 3.368 4.003 13.146 31.908 137.934 

1/ 30/2013 10:31:00 13.204 4.645 3.308 4.183 13.147 31.787 143.126 

1/ 30/2013 10:32:00 13.206 4.648 3.199 4.291 13.146 31.569 145.338 

1/ 30/ 2013 10:33:00 13.191 4.658 3.268 4.28 13.131 31.767 144.151 

1/ 30/2013 10:34:00 13.191 4.657 3.415 4.04 13.129 32.202 138.771 

1/30/2013 10:35:00 13.188 4.66 3.374 3.96 13.13 32.257 133.335 

1/30/2013 10:36:00 13.198 4.655 3.372 3.964 13.133 32.096 134.093 

1/ 30/ 2013 10:37:00 6.722 2.181 3.989 3.081 5.806 28.859 107.401 

1/ 30/2013 10:38:00 0.147 0.129 4.751 0.36 0.05 25.566 3.938 

1/ 30/ 2013 10:39:00 0. 128 0.124 4.747 0.247 0.027 25.314 0.162 

1/ 30/ 2013 10:40:00 0.128 0.121 4.744 0.25 1 0.02 25.184 0.157 

1/30/2013 10:41:00 0.128 0.12 4.744 0.246 0.019 25.08 0.155 

1/30/ 2013 10 42:001~0;;'~11:';:5"""--;:O~1;;;18;;--':;4-:;774--;;0;';2:::49;;-~0:;-0;;'1;;;9~--:;2747:98;;-~0;;'.;;;15'-';1"" 

1/ 30/2013 10:43:00 5.542 3.153 2.206 0.012 6.128 11.395 0.003 

1/30/ 2013 10:44:00 10.07 5.216 0 -0.309 10.038 0.842 -0.239 

1/ 30/ 2013 10:45:001.-:1;;0;;, .0;,;89"......-;;5,;;.2;;24;---""0.",00'"7,..., -0.328 10.058 0.756 -0.236 

1/30/2013 10:46:00 4.865 2.341 -0.004 1.03 4.006 0.68 31.881 

1/30/2013 10:47:00 0.137 0.131 -0.009 4.332 0.032 0.598 133.643 

1/30/2013 10:48:00 0.13 0.125 -0.008 4.526 0.016 0.529 1 136.515 1 

1/ 30/ 2013 10:49:00 4.771 3.104 2.475 4.521 1.977 6.795 134.76 

1/ 30/2013 10:50:00 10.073 5.222 4.765 4.528 10.009 24.275 135.454 

1/30/ 2013 10 51 001.....;1;;;0;;; .0;,92;;--;;5,;;.2;;2""1--4~7;,;64;;--..;4..;.5.;;26;;--;1;;;0;;;.0;;;63;;-....;;.4;;;4~0,;4-.;;13:;;6;;,4;;6"'8'1 

1/30/2013 10:52:00 2.164 0.977 1.473 2.899 5.577 14.244 95.702 

1/ 30/2013 10:53:00 0.108 0.098 -0.007 0.113 0.026 0.165 1.177 

1/ 30/ 2013 10 54 001~0;;';;;104;i;---;;0";0::;96;;--;;07:OOn.8;---;O;-:0:::4:'-~0:;-:0;;'1~6,.....-;;0-;1-i;29;;-~0;;'0;;;~3..., 

1/ 30/ 2013 10:55:00 6.813 2.809 1.585 1.036 5.45 10.707 10.335 

1/ 30/ 2013 10:56:00 13.099 4.641 3.3 3.585 13.018 31.902 110.428 

1/30/2013 10:57:00 13.096 4.651 3.372 3.772 13.03 31.928 122.943 

1/30/ 2013 10:58:00 13.104 4.65 3.338 3.733 13.03 31.977 122.347 

1/ 30/ 2013 10:59:00 13.092 4.654 3.345 3.721 13.02 31.904 121.108 

1/ 30/ 2013 11:00:00 13.112 4.644 3.286 3.821 13.041 31.677 123.508 

1/ 30/2013 11:01:00 13.111 4.644 3.303 3.722 13.037 31.779 118.43 

1/ 30/ 2013 11:02:00 13.108 4.644 3.274 3.812 13.027 31.705 121.99 

1/30/2013 11:03:00 13.088 4.65 3.319 3.728 13.006 31. 706 119.331 

1/ 30/ 2013 11:04:00 13.091 4.646 3.32 3.763 13.007 31.46 120.927 

1/ 30/ 2013 11:05:00 13.089 4.647 3.371 3.791 13.001 31.373 121.192 

1/ 30/ 2013 11:06:00 13.081 4.653 3.362 3.745 12.99 31.476 120.681 

1/ 30/ 2013 11:07:00 13.074 4.655 3.48 3.887 12.977 31.524 120.008 

1/30/2013 11:08:00 13.091 4.644 3.522 4.083 12.991 31.399 123.032 

1/30/2013 11:09:00 13.089 4.643 3.514 3.961 12.987 31.628 118.207 

1/ 30/2013 11:10:00 13.092 4.643 3.477 3.854 12.988 31.801 116.526 

1/ 30/ 2013 11:11:00 13.088 4.646 3.5 3.902 12.983 31.798 118.133 

1/ 30/2013 11:12:00 13.089 4.644 3.437 3.837 12.986 31.692 118.338 

1/ 30/ 2013 11:13:00 13.094 4.641 3.357 3.859 12.997 31.454 122.814 

THe 

PPM 

27.376 

26.955 

27.275 

28.202 

27.397 

28.429 

27.102 

26.051 

27.166 

27.278 

29.136 

29.833 

28.67 

25.349 

25. 355 

26.934 

28.59 

29.146 

28.273 

27.13 

25.294 

25.495 

22.03 

0.114 

-0.01 

-0.01 

-0.009 

-0.009 NOx bias 

-0.01 

-0.01 

-0.009 02/ 002 bias 

-0.008 

-0.003 

-0.003 CO bias 

-0.003 

19.541 

25.607 Span direct 

25.348 

25.339 

25.051 Zero direct 

24.82 

23.111 

23.199 

22.488 

21.792 

22.746 

21.705 Start NH3/RATA Run 1 

22.93 

21.613 

22.083 

22.368 

22.422 

21.728 

23.153 

21.646 

20.969 

21.505 

21.107 

22.807 
Date nme 

1/30/2013 11:14:00 

1/30/2013 11:15:00 

1/30/2013 11:16:00 

1/ 30/2013 11:17:00 

1/ 30/ 2013 11:18:00 

1/30/ 2013 11:19:00 

1/ 30/ 2013 11:20:00 

1/ 30/2013 11:21:00 

1/30/2013 11:22:00 

1/30/2013 11:23:00 

1/30/2013 11:24:00 

1/30/2013 11:25:00 

1/ 30/ 2013 11:26:00 

1/ 30/ 2013 11:27:00 

1/ 30/ 2013 11:28:00 

1/ 30/2013 11:29:00 

1/ 30/2013 11:30:00 

1/30/2013 11:31:00 

1/30/2013 11:32:00 

1/30/2013 11:33:00 

1/30/2013 11:34:00 

1/ 30/2013 11:35:00 

1/ 30/ 2013 11:36:00 

1/ 30/ 2013 11:37:00 

1/ 30/2013 11:38:00 

1/30/2013 11:39:00 

1/30/2013 11:40:00 

1/30/2013 11:41:00 

1/30/2013 11:42:00 

1/ 30/ 2013 11:43:00 

1/ 30/ 2013 11:44:00 

1/ 30/ 2013 11:45:00 

1/ 30/ 2013 11:46:00 

1/ 30/2013 11:47:00 

1/30/2013 11:48:00 

1/30/2013 11:49:00 

1/30/2013 11:50:00 

1/ 30/ 2013 11:51:00 

1/ 30/ 2013 11:52:00 

1/ 30/ 2013 11:53:00 

1/ 30/ 2013 11:54:00 

1/ 30/2013 11:55:00 

1/30/2013 11:56:00 

1/30/2013 11:57:00 

1/30/2013 11:58:00 

1/ 30/2013 11:59:00 

1/ 30/ 2013 12:00:00 

1/ 30/ 2013 12:01:00 

1/ 30/ 2013 12:02:00 

1/ 30/2013 12:03:00 

1/30/2013 12:04:00 

1/30/2013 12:05:00 

1/30/2013 12:06:00 

1/ 30/2013 12:07:00 

1/ 30/ 2013 12:08:00 

1/ 30/ 2013 12:09:00 

1/ 30/ 2013 12:10:00 

1/ 30/2013 12:11:00 

1/ 30/2013 12:12:00 

0, 

% 

13.106 

13.102 

13.093 

18.07 

13.137 

13.094 

13.044 

13.088 

13.087 

13.088 

13.087 

13.087 

13.098 

13.095 

13.102 

13.11 

13.096 

13.104 

13.091 

13.087 

13.071 

13.061 

13.052 

13.043 

13.017 

13.013 

13.016 

13.008 

15.067 

16.054 

13.066 

13.063 

13.058 

13.051 

13.061 

13.062 

13.064 

13.06 

13.058 

13.051 

13.033 

13.012 

12.99 

12.982 

12.979 

12.975 

12.956 

15.54 

13.008 

12.921 

12.915 

12.922 

12.919 

12.909 

12.907 

12.898 

12.905 

12.891 

12.892 

CO, 

% 

4.635 

4.636 

4.639 

1.699 

4.642 

4.64 

4.666 

4.642 

4.64 

4.642 

4.65 

4.655 

4.655 

4.662 

4.663 

4.659 

4.664 

4.657 

4.66 

4.659 

4.667 

4.668 

4.671 

4.67 

4.675 

4.676 

4.665 

4.676 

3.289 

3.082 

4.659 

4.664 

4.666 

4.668 

4.66 

4.661 

4.657 

4.66 

4.658 

4.656 

4.656 

4.658 

4.667 

4.668 

4.662 

4.661 

4.666 

3.093 

4.664 

4.67 

4.673 

4.666 

4.666 

4.671 

4.672 

4.679 

4.677 

4.688 

4.687 

NO, 

PPM 

3.262 

3.441 

3.491 

1.127 

3.354 

3.163 

3.372 

3.068 

3.102 

3.229 

3.242 

3.226 

3.187 

3.259 

3.204 

3.186 

3.246 

3.137 

3.341 

3.321 

3.329 

3.134 

3.203 

3.249 

3.288 

3.248 

3.236 

3.386 

2.457 

1.857 

3.222 

3.267 

3.231 

3.253 

3.181 

3.247 

3.229 

3.297 

3.332 

3.298 

3.247 

3.334 

3.247 

3.205 

3.24 

3.251 

3.234 

2.082 

3.065 

3.096 

3.125 

3.057 

2.957 

2.976 

3.139 

3.177 

3.16 

3.356 

3.105 

co 

PPM 

4.022 

4.033 

3.688 

1.933 

2.394 

3.84 

2.566 

3.368 

4.069 

3.935 

3.903 

3.402 

3.15 

3.134 

3.046 

2.908 

3.027 

3.048 

3.144 

3.003 

2.972 

2.911 

2.899 

2.856 

2.91 

2.835 

2.9 

2.714 

2.568 

1.461 

2.944 

3.102 

3.247 

3.307 

3.078 

3.09 

3.098 

3.12 

3.173 

3.115 

3.209 

3.172 

3.014 

2.898 

2.862 

2.937 

2.916 

2.292 

2.358 

2.538 

2.584 

2.602 

2.608 

2.651 

2.353 

2.048 

2.174 

2.166 

2.153 

0, 

% 

12.998 

12.995 

12.993 

12.991 

12.979 

12.985 

12.944 

12.988 

12.994 

12.993 

12.991 

12.983 

12.994 

12.994 

13 

13.009 

12.998 

13.009 

13.002 

12.977 

12.958 

12.951 

12.942 

12.931 

12.925 

12.919 

12.923 

12.912 

12.923 

12.938 

12.957 

12.948 

12.939 

12.939 

12.946 

12.95 

12.958 

12.944 

12.935 

12.93 

12.92 

12.915 

12.893 

12.883 

12.886 

12.875 

12.85 

12.841 

12.828 

12.826 

12.821 

12.82 

12.821 

12.803 

12.813 

12.806 

12.813 

12.791 

12.797 

NO, 

PPM 

31.196 

31.364 

31.744 

31.478 

32.334 

31.448 

33.246 

31.396 

30.883 

31.025 

31.361 

32.246 

32.342 

32.607 

32.651 

32.636 

32.503 

32.296 

32.366 

32.592 

32.674 

32.705 

32.85 

32.822 

32.866 

32.786 

32.576 

32.894 

32.832 

32.866 

32.781 

32.791 

32.616 

32.492 

32.497 

32.663 

32.713 

32.871 

32.913 

32.902 

32.74 

32.677 

32.929 

33.058 

33.058 

32.916 

32.996 

32.681 

33.051 

33.256 

33.096 

33.066 

32.658 

32.787 

32.725 

33.217 

32.938 

33.39 

33.025 

CO 

PPM 

128.068 

130.774 

118.054 

125.962 

102.426 

134.555 

93.294 

117.156 

141.297 

137.239 

136.13 

119.678 

113.337 

111.621 

110.02 

105.023 

109.341 

109.782 

113.377 

108.65 

110.151 

107.414 

108.428 

108.013 

108.304 

107.866 

108.248 

102.195 

105.467 

108.555 

106.172 

105.921 

111.534 

113.034 

107.914 

107.236 

105.445 

105.6 

104.86 

103.726 

105.801 

104.199 

104.484 

104.353 

101.123 

105.176 

103.649 

100.888 

104.972 

97.522 

100.253 

99.925 

99.689 

102.499 

99.009 

95.103 

96.956 

97.448 

96.209 

THe 

PPM 

24.119 

25.41 

21.614 

24.304 

16.593 

28.154 

14.74 

21.573 

28.124 

26.823 

27.151 

22.024 

20.433 

20.053 

19.719 

18.399 

19.841 

18.863 

20.54 

19.059 

20.008 

18.22 

18.771 

18.761 

18.458 

18.788 

19.073 

17.493 

17.734 

18.794 

18.454 

18.495 

19.941 

20.484 

19.093 

19.173 

18.181 

18.195 

17.421 

17.625 

18.613 

17.612 

17.459 

17.503 

17.166 

18.274 

17.661 

16.703 

18.374 

16.402 

16.88 

17.318 

17.257 

17.559 

16.809 

15.904 

15.943 

16.294 

15.988 
O2 CO2 NOK CO O2 NOK 

Date Time % % PPM PPM % PPM 

1/30/2013 12:13:00 12.897 4.682 3.212 2.204 12.789 33.008 

1/30/2013 12:14:00 12.886 4.694 3.341 2.114 12.763 33.27 

1/30/2013 12:15:00 12.886 4.691 3.154 2.139 12.769 32.928 

1/ 30/2013 12:16:00 12.881 4.696 3.287 2.035 12.761 33.51 

1/ 30/ 2013 12:17:00 12.877 4.696 3.311 2.127 12.757 33.333 

1/30/2013 12:18:00 10.975 4.613 1.93 1.976 11.058 19.781 

1/ 30/ 2013 12:19:00 9.889 5.24 0.006 -0.116 9.813 1.788 

1/30/2013 12:20:00 9.067 4.661 0.259 -0.337 9.802 1.491 

co 

PPM 

98.901 

93.463 

97.263 

94.082 

95.644 

81.79 

3.93 

-0.238 

1/30/2013 12:21:00 0.287 0.166 4.674 0.04 9.805 1.321 

1/30/2013 12:22:00"1 -0;.'::12~3""''''';0;;;.1:';4:;7-''';4.:;70;';9;'''''''''0::;.1:;9:''1--9;.;80;;5:'-'''';1;;.2;;1;:'1"" -0.284 

-0.243 

1/30/2013 12:23:00 0.124 0.142 2.385 1.407 4.265 12.347 

1/30/2013 12:24:00 0.101 0.138 0.003 4.337 0.D35 25.013 

1/30/ 2013 12:25:00 0.099 0.136 -0.007 4.494 0.01 25.029 

1/30/2013 12:26:00 4.995 2.914 -0.003 3.156 0.012 13.421 

1/ 30/2013 12:27:00 9.883 5.233 -0.011 -0.16 0.012 0.838 

1/30/2013 12 :2 00~:.;9;:96:::6:........:5:;;.2~4::.5 __ -O:::::: 0~13::...., -0.342 0.013 0.738 

1/30/2013 12:29:ooL

I....;:9:;:.9:;:9_....:5:;;.2;,:5;..1 __ -::::0:::: .0;.11;..J -0.344 0.012 0.693 

1/30/2013 12:30:00 1.919 1.06 -0.009 -0.296 0.014 0.457 

1/30/2013 12:31:00 0.1 0.118 -0.008 -0.038 0.012 0.157 

1/30/2013 12:32:00 0.1 0.12 -0.016 0.026 0.012 0.137 

-0.233 

0.049 

0.086 

24.872 

132.462 

136.145 

1 136.466 1 

115.002 

4.981 1 

0.013 

1/ 30/ 2013 12:33:00 7.027 3.979 2.43 1.905 5.053 10.742 33.034 

1/30/2013 12:34:00 9.968 5.255 4.731 4.452 9.937 24.089 134.3761 

1/30/2013 12:35:00 1.406 0.734 0.644 0.686 1.321 3.378 21.654 

THe 

PPM 

17.067 

15.104 

16.248 

15.365 

15.426 

15.539 

36.496 

40.776 

42.512 

43.883 NOx bias @ stack, 02 bias @ inlet 

44.686 

45.131 

45.597 NOx bias @ inlet;CO bias @ stack 

45.731 

45.875 

46.277 

46.744 CO bias inlet;02/C02 bias Stack 

46.433 

46.499 ITHe Mid 

31.913 

-0.007 

-0.005 ITHe Zero 

1.189 

1/ 30/ 2013 12:36:00 8.356 4.986 2.654 0.015 8.344 2.349 0.162 0.149 

1/30/2013 12:37:00 9.96 5.332 1.647 2.417 9.95 0.406 0.743 -0.145 

1/30/2013 12:38:00 9.993 5.27 4.835 4.595 9.973 21.77 73.938 -0.009 

1/30/2013 12:39:00 9.973 5.258 4.798 4.561 9.971 24.333 135.596 -0.006 

1/30/2013 12:40:00 9.967 5.254 4.794 4.545 9.947 24.546 135.954 -0.007 

1/30/2013 12 41 00~1-=9::9.:::44;--;:.5.;::2;:.54.;....-.;.4;;,7;:.85.;....-.:;4;;.5.:;4:....-:,;9:"9~4---=2::4;.:.5,;7::-~13;;5;:;9;;7;;2,....-0; . .;;00;:.6,.,loirect Span 

1/30/2013 12:42:00 6.984 3.544 3.741 4.349 8.915 24.126 133.542 -0.007 

1/30/2013 12:43:00 0.13 0.122 -0.008 0.642 0.139 1.089 24.912 -0.011 

1/ 30/ 2013 12:44 :00 ~1 ~0;;;1:,;02;--:;O:.:.1;22;..-.::-O;::.0;::1::..-0;:;05;:8;........;0::;0.::2::;8:....-0;;.::::11::;9:........:-O;.::0.:,13;..--O;."0.::12;...,loirect Zero 

1/30/2013 12:45:00 4.037 1.678 0.693 0.183 2.768 4.943 0.78 4.321 

1/30/2013 12:46:00 12.873 4.706 3.102 2.134 12.747 33.361 73.769 14.291 

1/30/2013 12:47:00 12.905 4.708 3.132 2.6 12.78 33.222 96.506 15.523 

1/30/2013 12:48:00 12.894 4.717 3.186 2.599 12.764 33.304 94.141 15.338 

1/30/2013 12:49:00 12.887 4.726 3.12 2.553 12.746 33.028 91.142 14.025 

1/30/ 2013 12:50:00 12.891 4.722 3.105 2.668 12.753 32.751 95.407 15.423 

1/30/ 2013 12:51:00 12.889 4.725 3.064 2.503 12.761 32.799 92.861 14.737 

1/ 30/ 2013 12:52:00 12.887 4.726 3.11 2.726 12.73 32.683 101.553 16.97 

1/30/ 2013 12:53:00 12.886 4.729 3.184 2.589 12.743 33.03 95.292 15.618 

1/ 30/2013 12:54:00 12.889 4.726 3.072 2.609 12.747 32.948 98.248 16.127 

1/30/2013 12:55:00 12.893 4.728 3.082 2.645 12.732 33.054 98.302 15.83 

1/30/2013 12:56:00 12.894 4.728 2.981 2.75 12.735 32.935 101.055 16.648 

1/30/2013 12:57:00 12.891 4.737 3.109 2.684 12.729 33.379 98.366 16.058 

1/ 30/2013 12:58:00 12.893 4.736 3.159 2.724 12.734 33.204 99.627 16.561 

1/30/2013 12:59:00 12.894 4.74 3.199 2.605 12.728 33.612 96.334 16.147 

1/30/2013 13:00:00 12.892 4.741 3.027 2.618 12.726 33.395 93.849 14.592 

1/30/2013 13:01:00 12.869 4.744 3.179 2.611 12.729 33.423 94.006 15.062 

1/30/2013 13:02:00 12.867 4.742 3.024 2.673 12.731 33.267 97.682 16.027 

1/30/2013 13:03:00 12.862 4.749 3.146 2.817 12.725 33.18 104.783 17.924 

1/30/2013 13:04:00 12.859 4.751 3.058 2.556 12.725 33.764 94.044 15.362 

1/30/2013 13:05:00 12.865 4.75 2.977 2.602 12.73 33.472 96.74 15.855 

1/ 30/2013 13:06:00 12.852 4.76 3.042 2.605 12.725 33.832 94.515 14.632 

1/30/ 2013 13:07:00 12.848 4.764 2.948 2.479 12.726 33.833 92.154 13.996 

1/ 30/2013 13:08:00 12.858 4.759 2.962 2.63 12.731 33.461 96.258 15.49 

1/ 30/2013 13:09:00 12.871 4.756 2.965 2.534 12.754 33.66 91.166 14.691 

1/ 30/2013 13:10:00 12.878 4.755 2.901 2.534 12.756 33.463 92.92 14.367 

1/30/2013 13:11:00 12.865 4.765 2.996 2.56 12.753 33.702 92.731 14.646 Start NH3/RATA Run 2 
Date Time 

1/30/2013 13:12:00 

1/30/2013 13:13:00 

1/30/2013 13:14:00 

1/30/2013 13:15:00 

1/30/2013 13: 16:00 

1/30/2013 13:17:00 

1/30/2013 13:18:00 

1/30/2013 13:19:00 

1/30/2013 13:20:00 

1/30/2013 13:21:00 

1/30/2013 13:22:00 

1/30/2013 13:23:00 

1/30/2013 13:24:00 

1/30/2013 13:25:00 

1/30/2013 13:26:00 

1/30/2013 13:27:00 

1/30/2013 13:28:00 

1/30/2013 13:29:00 

1/30/2013 13:30:00 

1/30/2013 13:31:00 

1/30/2013 13:32:00 

1/30/2013 13:33:00 

1/ 30/2013 13:34:00 

1/30/2013 13:35:00 

1/30/2013 13:36:00 

1/30/2013 13:37:00 

1/30/2013 13:38:00 

1/30/2013 13:39:00 

1/30/2013 13:40:00 

1/30/2013 13:41:00 

1/30/2013 13:42:00 

1/30/2013 13:43:00 

1/30/2013 13:44:00 

1/30/2013 13:45:00 

1/30/2013 13:46:00 

1/30/2013 13:47:00 

1/30/2013 13:48:00 

1/30/2013 13:49:00 

1/30/2013 13:50:00 

1/ 30/2013 13:51:00 

1/30/2013 13:52:00 

1/30/2013 13:53:00 

1/30/2013 13:54:00 

1/30/2013 13:55:00 

1/30/2013 13:56:00 

1/30/2013 13:57:00 

1/30/2013 13:58:00 

1/30/2013 13:59:00 

1/30/2013 14:00:00 

1/30/2013 14:01:00 

1/30/2013 14:02:00 

1/30/2013 14:03:00 

1/30/2013 14:04:00 

1/30/2013 14:05:00 

1/30/2013 14:06:00 

1/30/2013 14:07:00 

1/ 30/2013 14:08:00 

1/30/2013 14:09:00 

1/30/2013 14:10:00 

0, 

% 

12.873 

12.879 

12.862 

12.872 

12.881 

12.877 

12.868 

12.868 

12.863 

12.871 

12.885 

12.886 

12.882 

12.868 

12.88 

16.677 

13.13 

12.915 

12.885 

12.886 

12.889 

12.891 

12.886 

12.886 

12.888 

12.895 

12.911 

12.915 

12.933 

12.917 

12.923 

12.921 

12.925 

12.918 

12.928 

16.213 

13.322 

13.306 

13.633 

15.063 

15.99 

14.969 

14.009 

13.798 

13.802 

13.798 

13.794 

13.795 

13.796 

13.78 

13.768 

13.753 

13.75 

13.754 

13.755 

13.755 

13.812 

14.618 

15.595 

CO, 

% 

4.763 

4.762 

4.775 

4.772 

4.77 

4.775 

4.782 

4.784 

4.787 

4.785 

4.78 

4.776 

4.784 

4.795 

4.789 

2.436 

4.734 

4.762 

4.796 

4.795 

4.787 

4.789 

4.795 

4.798 

4.794 

4.792 

4.783 

4.784 

4.774 

4.783 

4.783 

4.785 

4.782 

4.789 

4.783 

2.832 

4.544 

4.552 

4.355 

3.487 

2.948 

3.572 

4.142 

4.268 

4.262 

4.269 

4.275 

4.277 

4.275 

4.281 

4.284 

4.289 

4.293 

4.287 

4.286 

4.284 

4.247 

3.757 

3.176 

NO, 

PPM 

2.976 

2.896 

3.032 

2.989 

2.923 

2.925 

2.969 

3.001 

3.089 

2.995 

2.925 

3.113 

2.967 

2.975 

2.984 

1.603 

2.844 

3.011 

3.252 

3.135 

3.089 

3.16 

3.134 

3.124 

3.044 

3.082 

3.059 

3.088 

3.014 

3.144 

2.95 

2.987 

2.939 

2.914 

2.962 

2.76 

5 

5 

4.631 

3.186 

2.646 

4.447 

5 

5 

4.779 

5 

4.938 

3.992 

5 

5 

3.795 

3.934 

5 

5 

5 

5 

5 

4.484 

1.838 

co 

PPM 

2.529 

2.642 

2.486 

2.645 

2.548 

2.663 

2.1 

2.227 

2.242 

2.142 

2.218 

2.232 

2.292 

2.111 

2.213 

1.739 

2.292 

3.217 

2.847 

2.83 

2.943 

2.679 

2.982 

2.775 

2.725 

2.943 

3.034 

2.734 

3.188 

3.032 

3.031 

2.837 

3.068 

2.931 

3.089 

1.51 

-0.054 

-0.065 

-0.065 

-0.022 

0.009 

-0.034 

-0.066 

-0.069 

-0.064 

-0.076 

-0.077 

-0.073 

-0.052 

-0.073 

-0.074 

-0.Q75 

-0.087 

-0.091 

-o.Q78 

-0.096 

-0.096 

-o.Q78 

0.Q28 

0, 

% 

12.757 

12.758 

12.752 

12.754 

12.768 

12.775 

12.773 

12.775 

12.777 

12.778 

12.786 

12.79 

12.803 

12.797 

12.803 

12.808 

12.82 

12.815 

12.771 

12.777 

12.789 

12.802 

12.79 

12.788 

12.788 

12.801 

12.817 

12.815 

12.834 

12.826 

12.832 

12.839 

12.838 

12.832 

12.845 

13.001 

13.215 

13.191 

13.666 

14.656 

15.085 

14.232 

13.405 

13.253 

13.279 

13.263 

13.248 

13.247 

13.251 

13.249 

13.249 

13.247 

13.246 

13.26 

13.245 

13.266 

13.358 

14.163 

14.92 

NO, 

PPM 

33.806 

33.647 

34.016 

33.869 

33.867 

33.504 

33.7 

33.41 

33.524 

33.748 

33.615 

33.682 

33.554 

33.865 

33.626 

33.92 

33.719 

33.737 

34.849 

34.627 

34.659 

34.718 

34.478 

34.723 

34.655 

34.261 

34.203 

34.436 

33.68 

34.068 

33.819 

34.014 

33.834 

34.101 

33.709 

41.253 

49.998 

49.998 

49.998 

49.815 

46.381 

49.998 

49.998 

49.998 

49.998 

49.998 

49.998 

49.998 

45.241 

49.998 

34.265 

43.544 

49.998 

49.998 

49.998 

49.998 

49.998 

45.508 

49.593 

co 

PPM 

90.76 

92.728 

88.842 

93.807 

90.637 

96.398 

92.09 

98.843 

97.093 

93.293 

98.398 

97.675 

102.762 

99.041 

100.764 

101.129 

98.506 

104.192 

91.151 

90.333 

93.374 

83.801 

93.158 

86.678 

84.488 

92.283 

94.009 

84.498 

98.575 

94.572 

97.343 

93.227 

101.378 

96.702 

102.503 

87.729 

9.633 

4.388 

4.958 

8.838 

15.77 

10.426 

5.854 

4.382 

4.165 

4.244 

4.191 

4.165 

4.132 

4.09 

4.052 

4.12 

4.092 

4.113 

4.092 

4.098 

4.147 

6.116 

11.247 

THC 

PPM 

14.408 

14.825 

12.945 

14.6 

14.007 

15.562 

14.647 

16.63 

14.989 

14.371 

16.304 

16.075 

16.603 

16.349 

16.627 

17.336 

15.643 

17.782 

14.584 

14.122 

14.561 

12.296 

14.967 

13.277 

12.67 

14.664 

14.4 

12.663 

16.258 

14.45 

15.782 

14.428 

16.594 

15.289 

17.179 

15.183 

0.824 

0.193 

0.108 

0.099 

0.097 

0.052 

0.069 

0.114 

0.048 

0.12 

0.094 

0.031 

0.Q35 

0.077 

0.122 

0.113 

0.091 

0.036 

0.039 

0.003 

-0.007 

-0.014 

-0.013 
Date Time 

1/30/2013 14:11:00 

1/30/2013 14:12:00 

1/30/2013 14:13:00 

1/ 30/2013 14:14:00 

1/ 30/ 2013 14:15:00 

1/ 30/ 2013 14:16:00 

1/ 30/ 2013 14:17:00 

1/30/2013 14:18:00 

1/30/2013 14:19:00 

1/30/2013 14:20:00 

1/30/2013 14:21:00 

1/30/2013 14:22:00 

1/30/2013 14:23:00 

1/ 30/2013 14:24:00 

1/30/ 2013 14:25:00 

1/30/2013 14:26:00 

1/30/2013 14:27:00 

1/30/2013 14:28:00 

1/30/2013 14:29:00 

1/30/2013 14:30:00 

1/30/2013 14:31:00 

1/30/2013 14:32:00 

1/ 30/ 2013 14:33:00 

1/ 30/ 2013 14:34:00 

1/30/2013 14:35:00 

1/30/2013 14:36:00 

1/30/2013 14:37:00 

1/30/2013 14:38:00 

1/30/2013 14:39:00 

1/ 30/ 2013 14:40:00 

1/30/ 2013 14:41:00 

1/30/2013 14:42:00 

1/30/2013 14:43:00 

1/30/2013 14:44:00 

1/30/2013 14:45:00 

1/30/2013 14:46:00 

1/30/2013 14:47:00 

1/30/2013 14:48:00 

1/30/2013 14:49:00 

1/30/2013 14:50:00 

1/30/2013 14:51:00 

1/30/2013 14:52:00 

1/30/2013 14:53:00 

1/30/2013 14:54:00 

1/30/2013 14:55:00 

1/30/2013 14:56:00 

1/ 30/2013 14:57:00 

1/30/2013 14:58:00 

1/30/ 2013 14:59:00 

1/30/2013 15:00:00 

1/30/2013 15:01:00 

1/30/2013 15:02:00 

1/30/2013 15:03:00 

1/30/2013 15:04:00 

1/30/2013 15:05:00 

1/30/2013 15:06:00 

1/30/2013 15:07:00 

1/30/2013 15:08:00 

1/30/2013 15:09:00 

0, 

% 

15.515 

14.527 

13.551 

13.312 

13.31 

13.328 

13.324 

13.332 

13.305 

13.324 

13.036 

12.956 

12.955 

12.95 

12.944 

12.957 

12.96 

12.961 

12.95 

12.95 

12.958 

12.96 

12.964 

12.97 

12.969 

12.984 

12.979 

12.971 

12.969 

12.98 

12.974 

12.973 

12.969 

17.286 

20.618 

20.632 

20.639 

18.859 

13.022 

12.985 

12.979 

12.981 

12.981 

12.978 

12.98 

12.989 

12.983 

12.979 

12.982 

12.993 

12.994 

12.996 

12.993 

12.996 

12.996 

16.887 

20.625 

20.623 

19.048 

CO, 

% 

3.233 

3.832 

4.417 

4.553 

4.555 

4.547 

4.551 

4.547 

4.567 

4.559 

4.74 

4.79 

4.791 

4.795 

4.8 

4.795 

4.797 

4.795 

4.806 

4.809 

4.806 

4.806 

4.806 

4.803 

4.805 

4.798 

4.804 

4.81 

4.813 

4.807 

4.812 

4.815 

4.82 

2.205 

0.299 

0.29 

0.289 

1.393 

4.797 

4.812 

4.819 

4.819 

4.818 

4.822 

4.822 

4.816 

4.823 

4.823 

4.823 

4.817 

4.817 

4.816 

4.819 

4.816 

4.816 

2.455 

0.308 

0.309 

1.04 

NO, 

PPM 

2.761 

1.547 

4.43 

2.86 

2.6C5 

2.562 

2.439 

2.431 

2.496 

2.471 

2.342 

2.621 

2.763 

2.731 

2.802 

2.79 

2.849 

2.775 

2.83 

2.868 

2.797 

2.903 

2.808 

2.88 

2.896 

2.774 

2.871 

2.853 

2.855 

2.787 

2.849 

2.771 

2.829 

1.422 

0.039 

0.029 

0.029 

0.566 

2.829 

2.931 

2.953 

2.919 

2.864 

2.989 

2.951 

3.051 

3.053 

3.103 

3.167 

3.017 

2.993 

3.036 

2.969 

2.95 

3.039 

1.676 

0.029 

0.027 

0.021 

co 

PPM 

-{).013 

0.532 

1.299 

4.273 

3.941 

3.695 

2.854 

2.893 

2.794 

2.469 

2.71 

2.568 

2.187 

2.443 

2.205 

2.318 

1.985 

2.063 

1.951 

2.089 

1.881 

1.979 

1.929 

1.936 

1.927 

1.769 

1.77 

1.645 

1.649 

1.796 

1.684 

1.668 

1.656 

1.042 

0.198 

0.166 

0.163 

0.247 

1.473 

1.835 

1.927 

1.697 

1.816 

1.785 

1.713 

1.768 

1.988 

1.815 

1.926 

1.839 

1.741 

1.762 

1.791 

1.632 

1.621 

1.237 

0.187 

0.151 

0.182 

0, 

% 

14.82 

13.892 

13.057 

12.896 

12.883 

12.895 

12.888 

12.911 

12.868 

12.873 

12.895 

12.88 

12.885 

12.882 

12.872 

12.89 

12.881 

12.894 

12.869 

12.873 

12.873 

12.888 

12.881 

12.882 

12.887 

12.915 

12.903 

12.887 

12.893 

12.903 

12.888 

12.883 

12.885 

12.88 

12.882 

12.883 

12.874 

12.872 

12.887 

12.898 

12.884 

12.878 

12.877 

12.882 

12.877 

12.895 

12.878 

12.877 

12.88 

12.904 

12.906 

12.894 

12.891 

12.903 

12.901 

12.899 

12.906 

12.92 

12.278 

NO, 

PPM 

43.062 

26.093 

31.928 

33.043 

33.7 

34.193 

34.683 

34.313 

34.837 

34.937 

34.246 

34.378 

34.567 

34.258 

34.614 

34.473 

34.715 

34.444 

34.653 

34.81 

34.64 

34.47 

34.579 

34.6C6 

34.77 

34.468 

34.735 

34.812 

34.785 

34.494 

34.852 

34.813 

34.932 

34.995 

35.017 

35.012 

35.066 

35.103 

34.857 

34.612 

34.814 

34.995 

34.805 

34.927 

35.139 

34.839 

34.931 

34.986 

35.043 

34.966 

34.808 

34.839 

35.099 

34.782 

34.995 

34.992 

35.022 

34.738 

32.537 

co 

PPM 

14.218 

5l.l71 

64.53 

143.529 

127.951 

116.359 

87.616 

91.226 

88.547 

72.603 

86.546 

90.918 

78.833 

89.338 

80.619 

85.71 

70.621 

72.43 

71.963 

74.991 

68.522 

75.477 

68.743 

65.114 

64.683 

60.818 

60.686 

58.213 

58.864 

62.488 

59.106 

57.773 

57.922 

54.937 

57.208 

53.57 

54.694 

53.709 

53.487 

60.309 

63.811 

55.375 

57.066 

55.592 

54.355 

53.057 

58.171 

53.845 

56.125 

55.121 

55.775 

54.248 

54.214 

56.66 

53.572 

55.185 

53.064 

55.692 

57.411 

THe 

PPM 

-0.001 

2.872 

6.836 

28.07 

22.805 

19.915 

13.244 

14.942 

13.937 

10.373 

13.965 

15.333 

12.054 

14.053 

12.059 

14.246 

10.097 

10.521 

10.735 

11.895 

9.369 

11.402 

9.713 

8.936 

8.663 

7.968 

8.095 

7.343 

7.645 

8.242 

7.514 

7.073 

7.362 

6.876 

7.255 

6.527 

6.943 

6.447 

6.457 

7.703 

8.915 

6.724 

6.975 

7.097 

6.65 

6.01 

7.316 

6.177 

6.823 

6.914 

6.618 

5.966 

6.572 

7.1 

6.688 

6.52 

6.41 

6.824 

7.041 
~ ~ N~ 00 ~ N~ 00 ~C 

Date Time % % PPM PPM % PPM PPM PPM 

1/30/2013 15:10:00 10.036 5.36 0.004 -0.201 9.918 l.758 17.447 1.929 

1/30/2013 15:11:00"1"':9::::.;'::964;';"-";5;';.3:::7;"7 ---;;'0;;'.0"'02:"'" -0.359 '-9:;;.:;;91;'7;--:1;';.0"8;;'6"" -0.306 -0.017 02/002 bias 

1/30/2013 15:12:00 16.338 2.224 0.01 -0.213 3.684 14.266 0.053 0.027 

1/30/2013 15:13:00 12.508 0.599 1.549 0.086 0.044 24.937 0.008 -0.016 

1/30/2013 15:14:00 0.154 0.243 4.753 0.176 0.027 24.897 -0.068 

1/30/2013 15: 15 :00"1 -0;;;.~12:';2~""'::0:;'.2;':4::--4;;':.=75;':9~-:0::';.1:;'9;;'7 --0;;;.;;:02,;6,.....~24;:..84~3-....:,-o::.;.0:::2:...., -0.016 

-0.017 NOx bias 

1/30/2013 15:16:00 0.122 0.237 2.117 1.694 0.026 10.892 37.806 -0.016 

1/30/2013 15:17:00 0.109 0.237 -0.005 4.4 0.023 0.588 133.628 -0.012 

1/30/2013 15:18:00 0.096 0.236 -0.003 4.48 0.023 0.492 1 134.928 1 -0.012 CO bias 

1/30/2013 15:19:00 8.023 4.462 3.087 4.465 6.784 15.357 120.254 1.337 

1/30/2013 15:20:00 9.962 5.376 4.774 4.483 9.916 24.314 131.986 6.634 

1/30/2013 15:21:00 1....;;9."9;:.63;--5;:.."37.;,7;--4'" .. . .;,76;,9;--4'" . .;.47:;;1;--;9;;.9;;.1;;9;-....;;2.;.4."3;;.33;--1;;3:,::5;.;.0:,::5"8.,1 6.217 Direct Span 

1/30/2013 15:22:00 1.72 1.025 1.337 2.601 4.425 12.006 99.079 5.908 

1/30/2013 15:23:00 0.097 0.22 -0.007 0.071 0.027 -0.034 2.183 7.536 

1/30/2013 15:24:00I L_0~.0::;9;;:6;--;i0:.;.2::;2;;-~-;:.0.;;;0~13;--;i-0::;.00~1 __ 0~.0;;:2;:;5~~-0~.0~6::;4_-:-~0.::;;06~4~ 1/30/2013 15:25:00 15.27 0.268 0.002 0.075 8.328 21.908 15.959 

1/30/2013 15:26:00 20.671 0.28 -0.008 0.135 12.853 34.665 54.829 

1/30/2013 15:27:00 20.664 0.291 0.002 0.142 12.876 34.328 60.801 

1/30/2013 15:28:00 16.858 2.556 1.397 0.446 12.867 34.775 59.342 

1/30/2013 15:29:00 12.999 4.818 2.92 1.566 12.861 34.912 57.861 

1/30/2013 15:30:00 12.985 4.829 2.916 1.626 12.859 34.99 55.125 

1/30/2013 15:31:00 12.986 4.832 2.891 1.845 12.869 34.74 62.078 

1/30/2013 15:32:00 12.986 4.834 2.998 1.911 12.871 34.753 64.065 

1/30/2013 15:33:00 12.975 4.841 2.992 2.075 12.864 34.572 67.739 

1/30/2013 15:34:00 12.974 4.845 3.099 1.969 12.857 35.123 63.355 

1/30/2013 15:35:00 12.983 4.839 2.899 2.003 12.873 34.573 69.013 

1/30/2013 15:36:00 12.971 4.847 2.909 2.048 12.858 35.013 67.871 

1/30/2013 15:37:00 12.963 4.855 2.986 2.098 12.849 34.952 68.574 

1/30/2013 15:38:00 12.973 4.85 2.936 1.769 12.854 35.348 62.83 

1/30/2013 15:39:00 12.964 4.856 3.027 1.577 12.849 35.665 53.688 

1/30/2013 15:40:00 12.964 4.857 2.915 1.823 12.849 35.207 57.744 

1/30/2013 15:41:00 12.963 4.856 2.977 1.766 12.846 35.407 60.532 

1/30/2013 15:42:00 12.957 4.862 3.024 1.994 12.837 35.155 65.095 

1/30/2013 15:43:00 12.954 4.863 3.021 2.159 12.834 35.107 69.023 

1/30/2013 15:44:00 12.962 4.858 2.946 2.365 12.856 34.594 70.946 

1/30/2013 15:45:00 12.959 4.861 3.036 2.622 12.841 34.478 82.941 

1/30/2013 15:46:00 12.962 4.859 3.01 2.617 12.854 34.567 80.973 

1/30/2013 15:47:00 12.952 4.863 3.046 2.681 12.841 34.536 84.374 

1/30/2013 15:48:00 12.965 4.855 3.047 2.586 12.861 34.555 81.331 

1/30/2013 15:49:00 12.957 4.864 3.152 2.853 12.834 34.574 82.496 

1/30/2013 15:50:00 12.969 4.852 3.121 2.835 12.858 34.68 82.876 

1/30/2013 15:51:00 12.958 4.858 3.193 2.669 12.842 34.8 76.373 

1/30/2013 15:52:00 12.978 4.841 3.071 2.766 12.86 34.566 82.194 

1/30/2013 15:53:00 12.992 4.834 3.084 2.798 12.878 34.278 82.594 

1/30/2013 15:54:00 12.98 4.843 3.101 2.85 12.868 34.439 86.852 

1/30/2013 15:55:00 18.424 1.61 1.065 1.714 12.863 34.54 86.315 

1/30/2013 15:56:00 13.595 4.497 2.601 1.517 12.878 34.499 83.912 

1/30/2013 15:57:00 12.991 4.832 2.999 2.542 12.898 34.042 89.061 

1/30/2013 15:58:00 12.988 4.834 3.088 2.775 12.897 33.928 95.149 

1/30/2013 15:59:00 12.976 4.842 3.055 2.564 12.887 34.476 90.059 

1/30/2013 16:00:00 12.986 4.836 3.055 2.468 12.905 34.146 89.103 

1/30/2013 16:01:00 12.996 4.83 2.93 2.558 12.911 34.107 91.678 

1/30/2013 16:02:00 13.008 4.824 2.929 2.731 12.921 33.881 94.668 

1/30/2013 16:03:00 13.009 4.82 2.994 2.738 12.921 33.836 96.194 

1/30/2013 16:04:00 13.007 4.819 2.919 2.592 12.919 34.144 90.202 

1/30/2013 16:05:00 13.024 4.806 2.892 2.771 12.925 33.759 96.4 

1/30/2013 16:06:00 16.679 2.632 1.649 2.074 12.922 34.019 90.534 

1/30/2013 16:07:00 14.233 4.109 2.285 1.556 12.921 33.935 96.934 

1/30/2013 16:08:00 13.003 4.813 2.86 2.455 12.922 33.971 94.896 

6.751 Direct Zero 

7.598 

6.903 

7.766 

7.412 

6.915 

6.431 

7.969 

8.168 

8.89 

8.223 

9.363 

9.025 

9.235 

8.325 

6.38 

6.678 

7.691 

8.431 

9.562 

9.567 

12.831 Start RATA Run 3 

12.289 

13.183 

12.502 

12.362 

11.861 

10.815 

12.556 

12.638 

13.63 

13.675 

12.437 

14.121 

15.642 

14.458 

13.734 

14.626 

15.59 

15.831 

14.482 

16.455 

14.498 

16.009 

15.61 
O2 CO2 NO~ CO 

Date Time % % PPM PPM 

1/30/2013 16:09:00 13.001 4.815 2.846 2.511 

1/30/2013 16:10:00 13.01 4.804 2.862 2.563 

1/30/2013 16:11:00 13.009 4.806 2.855 2.281 

1/30/2013 16:12:00 13.009 4.804 2.917 2.132 

1/30/2013 16:13:00 12.991 4.816 2.948 2.088 

1/30/2013 16:14:00 13.011 4.801 2.842 2.167 

1/30/2013 16:15:00 13.011 4.802 2.978 2.22 

1/30/2013 16:16:00 13.01 4.8 2.935 2.201 

1/30/2013 16:17:00 14.901 3.667 2.265 1.995 

1/30/2013 16:18:00 16.283 2.893 1.6 1.07 

1/30/2013 16:19:00 13.031 4.783 2.778 2.516 

1/30/2013 16:20:00 13.041 4.78 2.779 2.729 

1/30/2013 16:21:00 13.019 4.787 2.891 2.804 

1/30/2013 16:22:00 13.017 4.786 2.865 2.77 

1/30/2013 16:23:00 13.019 4.785 2.86 2.792 

1/30/2013 16:24:00 13.019 4.782 2.887 2.681 

1/30/2013 16:25:00 13.019 4.782 2.856 2.546 

1/30/2013 16:26:00 13.01 4.785 2.919 2.228 

1/30/2013 16:27:00 13.01 4.784 2.94 2.367 

1/30/2013 16:28:00 13.018 4.779 2.911 2.339 

1/30/2013 16:29:00 13.032 4.77 2.933 2.374 

1/30/2013 16:30:00 13.019 4.775 2.847 2.499 

1/30/2013 16:31:00 7.773 2.847 1.878 2.813 

1/30/2013 16:32:00 0.14 0.203 0.009 4.311 

1/30/2013 16:33:00 0.124 0.194 -0.002 4.462 

1/30/2013 16:34:00 4.842 2.722 0.003 3.353 

1/30/2013 16:35:001'"!-9~.~99:;:;2:---;:5"=.3~0';;'1-"";;';';;0:';;'" -0.12 

1/30/2013 16:36:00 4.528 2.432 2.44 -0.224 

1/30/2013 16:37:001'"! -0;;"~12;';6"""--;:O~.1'i;9~6 --4:;-.:;:77;;1---;:O~.1;;3':;'8' 

1/30/2013 16:38:00 12.225 0.211 2.114 0.192 

1/30/2013 16:39:00 20.745 0.223 0.021 0.179 

1/30/2013 16:40:00 18.804 1.4 0.596 0.337 

1/30/2013 16:41:00 13.047 4.749 2.766 2.433 

1/30/2013 16:42:00 13.008 4.765 2.846 2.91 

1/30/2013 16:43:00 13.009 4.765 2.804 2.767 

1/30/2013 16:44:00 13.005 4.768 2.852 2.894 

1/30/2013 16:45:00 12.997 4.772 2.865 2.67 

1/30/2013 16:46:00 12.986 4.78 2.982 2.308 

1/30/2013 16:47:00 12.988 4.777 2.984 2.337 

1/30/2013 16:48:00 13.008 4.764 2.915 2.24 

1/30/2013 16:49:00 13.007 4.765 2.929 2.311 

1/30/2013 16:50:00 13.008 4.76 2.95 2.367 

1/30/2013 16:51:00 18.594 1.449 0.898 1.453 

1/30/2013 16:52:00 17.451 2.186 1.131 0.844 

1/30/2013 16:53:00 13.054 4.737 2.866 3.349 

1/30/2013 16:54:00 13.031 4.746 2.885 3.377 

1/30/2013 16:55:00 13.044 4.739 2.916 3.447 

1/30/2013 16:56:00 13.046 4.736 2.925 3.715 

1/30/2013 16:57:00 13.054 4.731 2.835 3.57 

1/30/2013 16:58:00 13.069 4.719 2.935 4.149 

1/30/2013 16:59:00 13.059 4.722 2.99 4.125 

1/30/2013 17:00:00 13.058 4.721 2.921 4.093 

1/30/2013 17:01:00 13.049 4.729 2.782 3.744 

1/30/2013 17:02:00 13.037 4.733 2.766 3.736 

1/30/2013 17:03:00 13.012 4.743 2.93 3.358 

1/30/2013 17:04:00 17.193 2.277 1.27 2.16 

1/30/2013 17:05:00 13.058 4.732 2.865 2.992 

1/30/2013 17:06:00 13.011 4.739 2.872 3.533 

1/30/2013 17:07:00 13.007 4.743 2.956 3.401 

0, 

% 

12.921 

12.923 

12.925 

12.939 

12.922 

12.926 

12.925 

12.927 

12.922 

12.921 

12.953 

12.955 

12.943 

12.947 

12.951 

12.961 

12.955 

12.958 

12.954 

12.949 

12.97 

12.954 

8.02 

0.064 

1.532 

12.85 

12.945 

12.966 

12.951 

12.965 

12.968 

12.956 

12.946 

12.928 

12.934 

12.927 

12.926 

12.923 

12.923 

12.926 

12.926 

12.931 

12.927 

12.937 

12.936 

12.928 

12.942 

12.947 

12.956 

12.969 

12.961 

12.958 

12.949 

12.937 

12.922 

12.934 

12.924 

12.923 

12.92 

NO, 

PPM 

33.956 

33.962 

33.849 

33.755 

34.065 

33.937 

33.958 

34.071 

34.134 

34.175 

33.781 

33.68 

33.775 

33.907 

33.829 

33.94 

33.859 

33.823 

33.708 

33.902 

33.704 

33.793 

23.428 

1.266 

2.888 

32.443 

33.236 

33.046 

33.462 

33.5 

33.447 

33.552 

33.702 

33.756 

33.753 

33.927 

33.727 

34.237 

33.932 

33.992 

33.795 

33.759 

33.725 

33.607 

33.587 

33.828 

33.435 

33.376 

33.344 

32.64 

32.946 

32.981 

33.114 

33.171 

33.636 

33.176 

33.418 

33.489 

33.741 

CO 

PPM 

95.791 

96.947 

95.012 

97.188 

97.184 

97.335 

98.204 

95.769 

94.563 

96.756 

97.252 

100.191 

102.061 

99.441 

100.544 

97.583 

100.076 

98.218 

103.379 

102.722 

103.781 

104.082 

106.659 

132.844 

135.686 

114.291 

104.831 

106.918 

107.257 

102.342 

103.691 

105.309 

102.515 

104.91 

101.068 

101.921 

100.765 

100.31 

101.365 

98.258 

100.04 

102.93 

103.989 

104.861 

106.99 

102.214 

103.617 

112.398 

106.719 

119.524 

116.993 

116.35 

111.465 

116.323 

105.621 

113.615 

112.486 

111.499 

106.975 

THC 

PPM 

16.352 

15.718 

15.601 

16.126 

16.031 

15.696 

16.152 

15.024 

15.104 

16.255 

15.367 

17.025 

17.519 

16.876 

16.489 

16.151 

16.691 

16.429 

17.655 

17.831 

18.049 

17.638 

16.99 

0.762 

-0.008 Co bias 

13.057 

18.173 02/C02 bias 

18.688 

18.87 NOx bias 

17.612 

17.029 

18.338 

17.598 

18.25 

16.426 

17.746 

16.605 

17.133 

17.471 

15.939 

16.625 

17.761 

17.843 

18.584 

18.331 

17.435 

17.718 

20.045 

18.322 

22.121 

20.622 

21.034 

19.968 

21.036 

18.381 

20.142 

19.399 

20.47 

18.926 
~ ~ ~ ro ~ ~ 

Date Time % % PPM PPM % PPM 

1/30/2013 17:08:00 13.007 4.742 3.006 3.481 12.917 33.408 

1/30/2013 17:09:00 13.001 4.744 2.994 3.577 12.912 33.663 

1/30/2013 17:10:00 13.005 4.742 2.974 3.402 12.919 33.569 

1/30/2013 17:11:00 12.998 4.743 2.977 3.533 12.912 33.447 

1/30/2013 17:12:00 12.996 4.744 2.93 3.38 12.911 33.501 

1/ 30/ 2013 17:13:00 12.995 4.742 2.848 3.473 12.905 33.468 

1/ 30/2013 17:14:00 12.998 4.738 2.891 3.268 12.909 33.499 

1/30/2013 17:15:00 15.426 3.309 1.999 2.785 12.922 33.201 

1/30/2013 17:16:00 13.024 4.722 2.972 3.985 12.923 33.015 

1/30/2013 17:17:00 13.009 4.731 3.06 4.039 12.917 33.406 

1/30/2013 17:18:00 13.006 4.73 2.946 4.136 12.919 33.141 

1/30/2013 17:19:00 13.007 4.729 2.986 4.142 12.911 33.207 

1/30/2013 17:20:00 13.007 4.726 3.018 3.944 12.919 33.484 

1/30/2013 17:21:00 13.011 4.721 3.124 4.169 12.915 33.27 

1/30/ 2013 17:22:00 13.003 4.727 3.195 4.291 12.902 33.538 

1/30/2013 17:23:00 13.008 4.72 3.072 4.348 12.919 33.2 

1/30/2013 17:24:00 12.997 4.727 3.075 3.842 12.902 33.606 

1/30/2013 17:25:00 13.01 4.717 3.004 3.822 12.912 33.347 

1/30/2013 17:26:00 13.011 4.714 2.948 3.972 12.922 33.191 

1/30/2013 17:27:00 10.117 4.827 1.107 1.838 12.911 33.361 

1/30/2013 17:28:oo'"I..:9:::::;99;,1:.....--,;5~.2:;;76;,.........,0~0;;;1;,;l--. -0.294 12.918 33.343 

1/30/2013 17:29:00 4.475 2.365 2.483 -0.222 12.904 33.55 

1/30/2013 17:30:00'"1 --::0.;,1"3-....;;0~1:;;75;;-:.....4~. 7,;;6"'1:.....--,;0;;,;.1;,:;5;;;1..., 7 .103 20.528 

1/30/2013 17:31:00 0.125 0.165 1.639 1.962 0.041 0.196 

1/30/2013 17:32:00 0.1 0.161 0.005 4.379 0.025 0.091 

1/30/2013 17:33:00 0.099 0.157 0.001 4.473 0.D25 0.043 

1/30/2013 17:34:00 7.708 2.933 1.599 4.345 14.822 29.183 

1/30/2013 17:35:00 12.965 4.702 3.016 3.936 18.777 6.64 

1/30/2013 17:36:00 4.996 1.726 1.523 3.215 18.781 0.55 

1/ 30/ 2013 17:37:00 3.957 1.717 0.002 0.116 18.793 0.393 

1/ 30/2013 17:38:00 12.939 4.695 -0.004 0.007 18.8 39.713 

CO 

PPM 

110.269 

110.59 

108.859 

114.188 

108.565 

113.306 

108.312 

115.803 

118.881 

113.011 

116.046 

116.305 

111.23 

113.418 

113.986 

114.271 

113.217 

114.164 

117.373 

114.701 

113.938 

112.02 

110.214 

10.335 

-0.057 

-0.058 

54.679 

230.063 

236.689 

236.947 

236.93 

THC 

PPM 

19.359 

19.011 

18.323 

20.913 

18.497 

19.662 

18.776 

20.395 

21.815 

19.586 

19.975 

20.322 

19.816 

20.232 

20.745 

20.608 

19.21 

20.207 

21.827 

20.103 

20.397 02/C02 bias 

19.973 

22.352 NOx bias 

21.433 

18.999 

20.485 CO bias;lnlet Cal Zero 

20.926 

18.896 

21.335 

20.074 

22.222 

1/ 30/2013 17:39:00 12.961 4.704 L..~-0~.0'::'l:--_0:'.":00~6:----:1:;;8;.;.8~0::-1_-::4::::8'i .2::::85:':-_2::'3~7:':.2;.;;1~6 ... 1 21.081 Stack NOx/ro Cal Zero 

1/30/2013 17:40:00 12.956 4.71 3.641 1.752 12.988 30.899 237.154 19.33 

1/30/2013 17:41:00 12.955 4.708 4.776 5.58 9.971 24.033 166.668 21.798 

1/30/2013 17:42:00 16.94 2.202 4.777 9.426 9.97 24.332 135.249 20.025 

1/30/2013 17:43:00 15.687 2.109 L..4~.-::77'::5:--_9::' . .,:.48:::1:--.....,;:.9::;.9:::7:-.....;2';:4'::.3':'5 __ 1~3~5,;;.9::'04-::-'1 21.431 5tack Oirect High, Inlet Direct Mid 

1/30/2013 17:44:00 9.972 5.248 3.929 9.399 9.929 8.04 106.458 20.027 

1/30/2013 17:45:00 9.966 5.257 2.572 5.281 9.919 0.364 23.714 

1/30/ 2013 17:46:00'"1-'=9"'=.9"'6---=5"'=.2"57=--"'=2'=.5""4--':4""'.4"'=9'"1"" 9.919 0.263 4.88 

1/ 30/2013 17:47:00 4.079 2.036 3.373 2.182 11.735 16.984 26.603 

1/30/2013 17 48:oo'"I...;,0,;;1;,;3:....-0~.;;:16;;;2;-, 4.761 0.219 12.898 33.254 102.654 

1/30/2013 17:49:00 0.107 0.131 1.516 0.202 12.905 32.944 109.511 

1/30/2013 17:50:00'"1-0~.0:::9;,;9.....,....;;0~.1::;247-0 0.018 0.201 12.911 32.929 108.365 

1/30/2013 17:51:00 7.228 4.03 0.016 0.206 12.916 33.033 112.57 

1/30/2013 17:52:00 9.972 5.246 0.017 0.207 12.917 32.836 108.049 

1/30/2013 17:53:00 17.131 9.244 0.017 0.213 12.92 32.987 111.224 

1/ 30/2013 17:54:00 18.713 9.848 0.019 0.215 12.911 32.975 107.671 

1/30/2013 17 55 001'"-:1'i8;:,8":72:--....;;9;.;6~67,-, 0.062 0.21 12.922 32.989 108.53 

1/30/2013 17:56:00 11.552 5.793 0.11 0.218 12.923 32.735 115.603 

1/30/2013 17 57 oo'"I-:1;;:0'i.0~66;;-....;;5":.1i':347-0 0.12 0.218 12.923 32.879 107.818 

1/30/2013 17:58:00 9.702 5.14 0.157 0.228 12.923 32.986 110.738 

1/30/2013 17:59:00 1.19 5.143 0.169 0.23 12.924 32.521 115.207 

1/30/2013 17:59:20 7.156 5.143 0.15 0.25 12.922 32.873 112.196 

1/30/2013 17:59:30 9.268 5.143 0.156 0.204 12.923 33.011 108.967 

1/ 30/ 2013 17:59:40 7.902 5.143 0.157 0.235 12.998 32.58 107.544 

1/ 30/2013 17:59:50 1.349 5.143 0.163 0.237 13.09 30.828 110.241 

1/ 30/2013 18:00:00 9.788 5.144 0.169 0.242 13.168 30.782 116.198 

1/30/2013 18:00:10 18.134 5.144 0.156 0.26 13.273 29.109 116.926 

1/30/2013 18:00:20 18.728 5.145 0.148 0.255 13.329 27.14 125.057 

21.6 

21.642 Stack Mid;02/C02 bia s 

20.552 

19.733 NOx bias 

22.224 

21.088 02/C02 direct Zero 

22.603 

21.318 02/C02 Mid direct 

22.885 

20.872 

20.964 Cal High 

24.464 

21.743 02/C02 Mid 

22.86 

24.124 

23.15 

22.572 

21.452 

21.536 

25.366 

29.272 

26.027 
0 , 

Date TIme % 

1/ 30/ 2013 18:00:30 18.841 

1/30/2013 18:00:40 18.871 

1/ 30/ 2013 18:00:50 18.881 

1/30/ 2013 18:01:00 1 ... -:1~8,,:;8:::9::-, 1/ 30/2013 18:01:10 18.898 

1/30/2013 18:01:20 18.902 

1/ 30/2013 18:01:30 18.9 

1/ 30/ 2013 18:01 :40 17.124 

1/ 30/ 2013 18:01:50 15.231 

1/30/2013 18:02:00 15.054 

1/ 30/2013 18:02:10 15.019 

1/ 30/ 2013 18:02:201 15.012 

1/ 30/ 2013 18:02:30 14.413 

1/30/2013 18:02:40 11.662 

1/30/2013 18:02:50 11.263 

1/ 30/ 2013 18:03:00 11.186 

1/ 30/ 2013 18:03:10 11.178 

1/30/2013 18:03:201 11.178 

1/30/2013 18:03:30 11.177 

1/ 30/ 2013 18:03:40 10.734 

1/ 30/ 2013 18:03:50 9.542 

1/30/2013 18:04:00 9.352 

1/30/2013 18:04:10'"1""9;;;.;;;33:;3'""' 

1/ 30/ 2013 18:04:20 8.881 

1/ 30/ 2013 18:04:30 7.641 

1/ 30/ 2013 18:04:40 7.491 

1/30/2013 18:04:50 7.459 

1/ 30/ 2013 18:05:00r

l -:7"'.4~58~ 

1/ 30/ 2013 18:05:10 7.29 

1/ 30/ 2013 18:05 :20 4.529 

1/30/2013 18:05:30 3.883 

1/ 30/ 2013 18:05:40 3.804 

1/ 30/2013 18:05:50 ... 1_3::-7~7::6 ..... 

1/ 30/ 2013 18:06:00 4.701 

1/30/2013 18:06:10 9.245 

1/ 30/2013 18:06:20 9.921 

1/ 30/ 2013 18:06:30 10.024 

1/ 30/ 2013 18:06:40 10.04 

1/30/2013 18:06:501 10.054 

1/30/2013 18:07:00 10.046 

1/ 30/ 2013 18:07:10 9.476 

1/ 30/ 2013 18:07:20 13.669 

1/30/2013 18:07:30 14.777 

1/30/2013 18:07:40 14.888 

1/ 30/ 2013 18:07:50 14.915 

1/ 30/ 2013 18:08:001 14.916 

1/30/2013 18:08:10 14.916 

1/30/2013 18:08:20 13.002 

1/ 30/ 2013 18:08:30 11.329 

1/ 30/ 2013 18:08:40 11.162 

1/ 30/ 2013 18:08:50 11.128 

1/30/2013 18:09:001 11.128 

1/ 30/ 2013 18:09:10 11.125 

1/30/2013 18:09:20 10.401 

1/30/2013 18:09:30 9.412 

1/30/2013 18:09:40 9.326 

1/ 30/2013 18:09:50 9.318 

1/ 30/2013 18:10:00 9.315 

1/ 30/ 2013 18:10:10 9.307 

CO, 

% 

5.144 

5.143 

5.145 

5.143 

5.142 

5.145 

5.142 

5.144 

5.144 

5.143 

5.142 

5.142 

5.144 

5.144 

5.143 

5.143 

5.142 

5.144 

5.144 

5.144 

5.143 

5.143 

5.145 

5.143 

5.145 

5.144 

5.143 

5.144 

5.143 

5.142 

5.143 

5.141 

5.143 

5.142 

5.143 

5.144 

5.142 

5.141 

5.143 

5.142 

5.141 

5.143 

5.144 

5.143 

5.142 

5.142 

5.142 

5.142 

5.142 

5.143 

5.143 

5.144 

5.142 

5.143 

5.142 

5.143 

5.14 

5.142 

5.139 

NO, 

PPM 

0.144 

0.158 

0.172 

0.178 

0.185 

0.181 

0.175 

0.182 

0.191 

0.179 

0.179 

0.163 

0.169 

0.177 

0.181 

0.176 

0.154 

0.152 

0.157 

0.173 

0.154 

0.149 

0.143 

0.139 

0.128 

0.13 

0.118 

0.128 

0.139 

0.156 

0.145 

0.118 

0.117 

0.116 

0.107 

0.107 

0.118 

0.102 

0.104 

0.109 

0.119 

0.113 

0.116 

0.106 

0.103 

0.121 

0.115 

0.111 

0.103 

0.11 

0.109 

0.099 

0.117 

0.097 

0.109 

0.142 

0.131 

0.12 

0.142 

co 

PPM 

0.232 

0.23 

0.243 

0.26 

0.261 

0.248 

0.231 

0.231 

0.232 

0.248 

0.248 

0.23 

0.257 

0.237 

0.232 

0.235 

0.25 

0.271 

0.271 

0.255 

0.243 

0.257 

0.264 

0.299 

0.268 

0.241 

0.236 

0.253 

0.264 

0.263 

0.266 

0.264 

0.261 

0.252 

0.248 

0.285 

0.274 

0.281 

0.277 

0.265 

0.277 

0.275 

0.282 

0.308 

0.267 

0.281 

0.285 

0.284 

0.289 

0.299 

0.296 

0.315 

0.29 

0.299 

0.285 

0.301 

0.302 

0.304 

0.275 

0 , 

% 

13.424 

13.558 

13.679 

13.787 

13.896 

14.055 

14.247 

14.439 

14.659 

14.904 

15.292 

15.816 

16.299 

16.273 

16.272 

16.289 

16.297 

16.312 

16.308 

16.298 

16.319 

16.323 

16.331 

16.346 

16.321 

16.337 

16.345 

16.346 

16.331 

16.337 

16.345 

16.346 

16.346 

16.367 

16.347 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.346 

16.345 

16.346 

16.343 

16.345 

16.342 

16.337 

16.341 

16.332 

NO, 

PPM 

27.384 

28.153 

27.9 

26.984 

25.596 

24.511 

24.225 

24.314 

23.85 

23.24 

24.239 

34.274 

32.833 

29.36 

29.311 

29.284 

29.095 

28.983 

28.699 

28.754 

28.722 

28.656 

28.609 

28.461 

28.434 

28.491 

28.394 

28.388 

28.356 

28.37 

28.334 

28.318 

28.255 

28.212 

28.078 

28.113 

28.139 

28.176 

28.134 

28.082 

28.081 

28.055 

28.045 

28.036 

28.002 

28 

27.995 

27.973 

27.94 

27.931 

27.919 

27.891 

27.871 

27.849 

27.856 

27.852 

27.829 

27.802 

27.777 

CO 

PPM 

138.892 

135.023 

113.901 

85.537 

64.683 

57.286 

57.293 

57.685 

56.031 

53.659 

52.386 

49.128 

40.649 

37.734 

39.406 

42.694 

45.139 

46.04 

47.14 

48.476 

49.053 

49.512 

50.083 

50.392 

51.281 

51.726 

52.171 

52.314 

52.465 

52.754 

52.76 

53.058 

53.063 

53.532 

53.542 

54.05 

54.141 

54.29 

54.288 

54.289 

54.426 

54.338 

54.578 

54.323 

54.432 

54.438 

54.741 

54.742 

54.742 

54.742 

54.735 

54.436 

54.775 

55.041 

55.193 

55.192 

55.341 

55.344 

55.345 

THC 

PPM 

35.58 

47.625 

34.36 

16.277 

7.582 

3.649 

4.332 

4.833 

4.219 

3.452 

3.187 

3.203 

2.737 

0.873 

1.147 

1.106 

0.791 

0.772 

0.857 

0.976 

1.106 

1.088 

1.1 

1.099 

1.123 

1.239 

1.253 

1.224 

1.259 

1.299 

1.291 

1.301 

1.312 

1.343 

1.355 

1.416 

1.397 

1.404 

1.4 

1.353 

1.366 

1.357 

1.322 

1.345 

1.363 

1.384 

1.403 

1.454 

1.479 

1.464 

1.533 

1.524 

1.464 

1.426 

1.476 

1.512 

1.457 

1.452 

1.413 

100% 

80% 

60% 

50% 

40% 

20% 

Mid 

80% 

60% 
0, 

Date Time % 

1/30/2013 18:1O:20L!_9~~30~1,-, 

1/30/2013 18:10:30 9.061 

1/30/2013 18:10:40 7.698 

1/30/2013 18:10:50 7.482 

1/ 30/2013 18:11:00 7.441 

1/ 30/ 2013 18:11:10 7.432 

1/ 30/2013 18:11 :20 "!-7:::""43~4;-' 

1/30/2013 18:11:30 6.8 

1/30/2013 18:11:40 4.212 

1/30/2013 18:11:50 3.842 

1/30/2013 18:12:00 3.786 

1/30/2013 18:12:10 3.774 

1/ 30/2013 18:12:20 3.774 

1/ 30/ 2013 18:12:30 3.774 

1/30/2013 18:12:40 3.776 

1/30/2013 18 12 50"!-=-3~77::-:1""" 

1/30/2013 18:13:00 5.128 

1/30/2013 18:13:10 9.377 

1/30/2013 18:13:20 9.913 

1/30/2013 18:13:30 10.003 

1/30/2013 18:13:40 10.018 

1/ 30/2013 18:13:50! 10.038 

1/30/2013 18:14:00 9.996 

1/30/2013 18:14:10 12.917 

1/30/2013 18:14:20 14.771 

1/30/2013 18:14:30 14.918 

1/30/2013 18:14:40 14.946 

1/30/2013 18:14:50 14.962 

1/30/2013 18:15:oo! 14.965 

1/30/2013 18:15:10 14.05 

1/30/2013 18:15:20 11.521 

1/30/2013 18:15:30 11.214 

1/30/2013 18:15:40 11.167 

1/30/2013 18:15:50 11.152 

1/30/2013 18:16:00! 11.152 

1/30/2013 18:16:10 10.967 

1/30/2013 18:16:20 9.644 

1/30/ 2013 18:16:30 9.344 

1/30/2013 18:16:40 9.318 

1/30/2013 18:16:50 9.308 

1/30/2013 18:17:00 9.299 

1/30/2013 18:17:10 9.294 

1/30/2013 18:17:20 9.293 

1/30/2013 18:17:30r! -:9:".2;;;94~ 

1/30/2013 18:17:40 8.868 

1/30/2013 18:17:50 7.623 

1/30/2013 18:18:00 7.471 

1/30/ 2013 18:18:10 7.437 

1/30/2013 18:18:20 7.433 

1/30/2013 18:18:30"!-7:::.""43"'3;-' 

1/30/2013 18:18:40 7.432 

1/30/2013 18:18:50 7.433 

1/30/2013 18:19:00 7.432 

1/30/2013 18:19:10 6.845 

1/30/2013 18:19:20 4.216 

1/ 30/ 2013 18:19:30 3.842 

1/30/ 2013 18:19:40r

! "';3:;;7:::8~2' 

1/30/2013 18:19:50 4.475 

1/30/2013 18:20:00 9.261 

CO, 

% 

5.14 

5.139 

5.14 

5.14 

5.141 

5.139 

5.139 

5.139 

5.138 

5.139 

5.139 

5.139 

5.14 

5.138 

5.137 

5.139 

5.137 

5.136 

5.138 

5.138 

5.139 

5.137 

5.138 

5.136 

5.135 

5.135 

5.135 

5.132 

5.132 

5.132 

5.132 

5.132 

5.131 

5.131 

5.132 

5.13 

5.131 

5.131 

5.129 

5.132 

5.132 

5.13 

5.126 

5.126 

5.128 

5.127 

5.126 

5.127 

5.126 

5.123 

5.122 

5.124 

5.122 

5.123 

5.121 

5.122 

5.124 

5.121 

5.121 

NO, 

PPM 

0.113 

0.104 

0.107 

0.108 

0.125 

0.126 

0.112 

0.128 

0.14 

0.133 

0.13 

0.123 

0.134 

0.134 

0.14 

0.14 

0.123 

0.11 

0.13 

0.149 

0.137 

0.123 

0.11 

0.092 

0.084 

0.081 

0.071 

0.076 

0.076 

0.068 

0.069 

0.073 

0.074 

0.078 

0.076 

0.076 

0.079 

0.076 

0.073 

0.072 

0.07 

0.071 

0.075 

0.076 

0.082 

0.067 

0.066 

0.064 

0.07 

0.059 

0.061 

0.061 

0.059 

0.058 

0.056 

0.058 

0.07 

0.077 

0.063 

co 

PPM 

0.297 

0.276 

0.283 

0.303 

0.319 

0.311 

0.285 

0.285 

0.282 

0.301 

0.309 

0.3 

0.29 

0.289 

0.277 

0.279 

0.296 

0.308 

0.315 

0.305 

0.3 

0.297 

0.289 

0.302 

0.323 

0.326 

0.297 

0.303 

0.302 

0.299 

0.337 

0.329 

0.307 

0.301 

0.311 

0.325 

0.318 

0.306 

0.326 

0.308 

0.318 

0.325 

0.283 

0.289 

0.331 

0.323 

0.31 

0.323 

0.317 

0.316 

0.312 

0.338 

0.334 

0.341 

0.324 

0.322 

0.297 

0.303 

0.344 

0, 

% 

16.322 

16.332 

16.322 

16.321 

16.321 

16.321 

16.32 

16.321 

16.326 

16.322 

16.322 

16.322 

16.344 

18.651 

20.455 

20.632 

20.658 

20.688 

20.689 

20.688 

20.689 

20.689 

20.69 

20.689 

20.688 

20.69 

20.69 

20.69 

20.689 

20.689 

20.689 

20.689 

20.689 

20.689 

20.688 

20.689 

20.688 

20.688 

20.688 

20.688 

20.689 

20.689 

20.689 

20.689 

20.689 

20.689 

20.689 

20.689 

20.689 

20.689 

20.688 

20.688 

20.689 

20.683 

20.679 

20.672 

20.665 

20.665 

20.666 

NO, 

PPM 

27.773 

27.782 

27.771 

27.735 

27.728 

27.729 

27.725 

27.722 

27.714 

27.659 

27.665 

27.644 

27.657 

23.184 

5.746 

1.478 

1.193 

1.074 

0.989 

0.922 

0.869 

0.827 

0.81 

0.766 

0.735 

0.706 

0.675 

0.648 

0.633 

0.61 

0.583 

0.565 

0.551 

0.539 

0.529 

0.53 

0.517 

0.487 

0.471 

0.471 

0.461 

0.444 

0.433 

0.417 

0.42 

0.4 

0.394 

0.385 

0.375 

0.364 

0.352 

0.338 

0.337 

0.329 

0.32 

0.32 

0.31 

0.305 

0.303 

co 

PPM 

55.493 

55.493 

55.638 

55.637 

55.636 

55.795 

55.791 

56.087 

55.936 

55.792 

55.941 

55.943 

55.946 

56.318 

GO. 172 

48.156 

31.705 

15.277 

6.542 

3.346 

1.858 

1.117 

0.686 

0.543 

0.392 

0.392 

0.253 

0.248 

0.246 

0.388 

0.248 

0.393 

0.39 

0.387 

0.241 

0.392 

0.245 

0.242 

0.241 

0.242 

0.242 

0.243 

0.241 

0.242 

0.245 

0.241 

0.245 

0.246 

0.242 

0.236 

0.236 

0.236 

0.237 

0.236 

0.24 

0.239 

0.24 

0.242 

0.241 

THe 

PPM 

1.408 

1.476 

1.56 

1.578 

1.463 

1.495 

1.513 

1.515 

1.531 

1.572 

1.52 

1.487 

1.484 

1.506 

2.01 

90.973 

99.997 

99.997 

99.997 

94.257 

61.86 

23.452 Mid 

12.889 

12.889 

12.888 

12.889 

12.89 

12.889 

12.889 

12.89 

12.889 

12.889 

12.887 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.888 

12.889 

12.888 

12.888 

12.888 

12.887 

12.887 

12.888 

12.888 

12.887 

12.887 

12.888 

12.888 

12.888 

12.887 

50% 

40% 

20% 

80% 

60% 

50% 

40% 

20% 
0, CO, NO, CO 0, NO, CO THe 

Date Time % % PPM PPM % PPM PPM PPM 

1/30/2013 18:20:10 10.055 5.122 0.065 0.343 20.664 0.29 0.241 12.887 

1/30/2013 18:20:201 10.165 5.121 0.057 0.35 20.663 0.28 0.242 12.886 Mid 

1/30/2013 18:20:30 10.189 5.122 0.061 0.328 20.664 0.275 0.237 12.887 
~ ~ N~ 00 ~ ~ 00 THC 

Date Time % % PPM PPM % PPM PPM PPM 

1/ 31/ 2013 7:58:00 13.924 0.508 0 0.36 20.257 -0.021 1.17 2.669 

2.607 

2.604 

2.64 

1/ 31/2013 7:59:00 0.368 0.092 -0.019 0.029 2.46 -0.128 0.645 

1/31/ 2013 8:00:00 0.113 0.077 -0.016 -0.022 0.062 -0.141 -0.026 

1/31/2013 8:01:00 0.109 0.073 -0.015 -0.015 0.048 -0.086 -0.026 

1/ 31/ 2013 8:02:00 0.108 0.071 -0.012 -0.011 0.036 0.055 -0.03 1.319 N2/ NO Mode 

1/31/2013 8:03:00 0.108 0.067 -0.021 -0.022 0.035 0.04 -0.031 73.686 

1/31/2013 8:04:00 rl-0::'.~1O~7~--;;0:'i0';;647---~0.'i:0~17~--;;-0"'.0;::0~4-~0::'.0~3:;;5-~0~.0~5;;'7---'i:0.'i:0;;;31~ 

1/31/2013 8:05:00 15.956 8.279 2.909 4.741 10.411 2.847 64.422 

61.957 N2/NO Mode;02/OO2/OO Cal Zero 

1.42 

1/31/2013 8:06:00 18.963 9.625 4.821 9.367 18.829 4.869 232.191 0.614 

1/31/2013 8:07:00 .....:1;;:8;;;.9:i:-75;---;;9:'i.6,,65;-1-4;:..8:;;1;,;6-4....,;9;.;.4~39~ 18.878 4.876 237.306 

1/31/2013 8:08:00 L..;1;;:8;.:;.9;;81;-....,;9,;.;.6~6;;.2....1 4.821 9.439 20.474 4.871 237.544 

0.056 NO/NOx Mode 

-0.167 02/C02/OO Cal High 

1/31/2013 8:09:00 18.52 9.417 4.814 9.45 20.608 4.872 237.422 -0.18 

1/31/2013 8:10:00 10.265 5.102 4.815 9.454 11.825 4.874 I 205.061 -0.181 NO/NOx Mode 

1/31/2013 8:11:00 10.117 5.097 4.816 7.343 11.053 4.869 87.309 -0.187 

1/31/2013 8:12:00 10.109 5.095 4.829 4.478 11.052 4.873 I 135.37 -0.046 NO/ NO Mode 

1/ 31/2013 8:13:00 10.104 5.091 2.478 4.457 11.16 2.63 136.057 -0.002 02/C02/CO Mid 

1/ 31/ 2013 8:14:00 12.55 4.64 -0.003 4.401 11.075 0.064 112.873 -0.004 

1/ 31/2013 8:15:00 13.236 4.475 0.002 4.492 1.475 0.069 28.193 -0.007 N02/ NO Mode 

1/31/ 2013 8:16:00 13.236 4.471 3.231 4.899 0.056 3.386 0.737 -0.009 

1/ 31/2013 8:17:00 13.226 4.479 3.854 4.514 0.049 3.928 0.082 -0.009 N02/ NOx Mode @ 817 

1/31/2013 8:18:00 13.221 4.478 1.807 4.254 0.029 2.102 0.009 -0.01 

1/ 31/2013 8:19:00 13.233 4.467 -0.008 4.534 0.029 0.077 -0.001 -0.009 

1/31/2013 8:20:00 13.225 4.472 -0.013 4.434 0.028 0.069 -0.006 -0.009 NOx/02Cal Zero 

1/31/2013 8:21:00 13.223 4.473 

1/31/2013 8:22:00 13.218 4.474 

1/31/2013 8:23:00 12.799 4.251 

1/31/2013 8:24:00 12.852 4.414 

1/31/2013 8:25:00 13.217 4.469 

1/31/2013 8:26:00 13.211 4.472 

1/31/2013 8:27:00 13.206 4.477 

1/31/2013 8:28:00 13.19 4.486 

1/ 31/ 2013 8:29:00 13.202 4.481 

1/ 31/2013 8:30:00 13.218 4.471 

1/ 31/ 2013 8:31:00 13.23 4.466 

1/31/2013 8:32:00 11.587 4.349 

1/ 31/ 2013 8:33:00 10.067 5.079 

1/ 31/2013 8:34:00 I 10.068 5.085 

1/ 31/ 2013 8:35:00 5.836 2.795 

1/ 31/2013 8:36:00 0.141 0.082 

1/31/2013 8:37:00 I 0.126 0.072 

1/31/2013 8:38:00 0.126 0.07 

1/31/2013 8:39:00 0.118 0.068 

1/31/2013 8:40:00 0.101 0.067 

1/31/2013 8:41:00 4.39 1.693 

1/31/2013 8:42:00 13.141 4.468 

1/31/2013 8:43:00 13.186 4.47 

1/31/2013 8:44:00 13.183 4.479 

1/31/2013 8:45:00 13.195 4.476 

1/ 31/ 2013 8:46:00 13.177 4.488 

1/31/2013 8:47:00 13.18 4.488 

1/ 31/ 2013 8:48:00 13.191 4.482 

1/ 31/ 2013 8:49:00 13.187 4.486 

1/ 31/ 2013 8:50:00 13.191 4.483 

1/31/2013 8:51:00 13.181 4.489 

1/31/2013 8:52:00 13.164 4.498 

1/31/2013 8:53:00 13.161 4.5 

1/31/2013 8:54:00 17.665 1.889 

1/31/2013 8:55:00 13.231 4.494 

2.966 4.245 

4.782 3.872 

4.782 3.666 

4.788 3.59 

3.231 3.652 

2.56 3.601 

2.542 3.681 

3.056 3.245 

3.112 3.291 

3.098 3.439 

3.11 4.286 

2.175 2.777 

-0.001 -0.11 

-0.007 -0.37 

1.903 -0.281 

4.769 0.137 

4.783 0.198 

1.51 2.137 

-0.012 4.409 

-0.012 4.484 

0.951 4.199 

2.986 2.777 

2.968 3.013 

3.079 2.684 

3.049 2.775 

3.08 2.835 

3.136 

3.026 

3.2 

3.144 

3.202 

3.188 

3.163 

1.266 

3.154 

2.565 

2.761 

2.616 

2.91 

2.894 

2.494 

2.485 

1.498 

1.849 

9.321 2.48 -0.04 -0.008 

19.138 4.85 -0.021 -0.009 

19.091 33.208 0.071 -0.01 

19.39 48.937 0.06 -0.009 NOx/02 Cal High 

12.251 22.504 0.022 -0.01 

16.767 23.882 -0.002 -0.01 

18.882 24.479 0.021 -0.011 NOx Mid 

18.883 7.823 0.029 -0.011 02 Cal High 

11.201 0.227 -0.053 -0.011 

10.047 0.182 -0.056 -0.011 02 Mid 

4.522 0.18 -0.038 -0.011 

3.547 0.269 1.83 -0.012 ITHC Zero 

9.961 0.212 1.636 8.374 

9.971 0.204 -0.324 83.091 02 bias 

4.941 10.747 -0.287 84.567 

0.057 24.676 -0.04 84.706 

0.032 24.704 -0.011 84.737 NOx bias 

0.03 8.623 46.602 84.445 

0.026 0.183 135.372 84.47 

0.026 0.161 I 135.972 I 84.458 CO bias 

0.027 0.147 118.114 83.888 

0.027 0.135 6.722 84.228 

0.026 0.113 0.092 85.037 

0.026 0.126 0.091 85.007 

0.026 0.126 0.088 84.807 

2.222 3.251 0.244 85.008 ITHC High 

5.491 14.166 5.581 58.552 

0.036 0.157 -0.031 46.871 

0.026 0.136 -0.02 46.63 

0.026 0.129 -0.009 46.527 ITHC Mid 

2.465 0.13 0.029 38.469 

0.031 0.134 -0.058 25.219 

0.027 0.116 -0.039 25.349 ITHC low 

6.971 14.556 21.119 25.263 

13 31.498 97.914 20.687 
O2 CO2 NO~ CO 

Date nme % % PPM PPM 

1/ 31/ 2013 8:56:00 13.149 4.508 3.112 2.283 

1/ 31/2013 8:57:00 13.14 4.513 3.156 2.253 

1/ 31/ 2013 8:58:00 13.147 4.51 3.024 2.341 

1/31/2013 8:59:00 13.161 4.501 2.939 2.351 

1/31/2013 9:00:00 13.161 4.503 2.972 2.446 

1/31/ 2013 9:01:00 13.16 4.504 3.065 2.506 

1/ 31/ 2013 9:02:00 13.15 4.51 3.023 2.557 

1/ 31/ 2013 9:03:00 13.156 4.508 2.926 2.556 

1/31/2013 9:04:00 13.157 4.507 2.98 2.55 

1/31/2013 9:05:00 16.644 2.466 1.636 1.771 

1/31/2013 9:06:00 13.213 4.513 3.085 2.314 

1/31/ 2013 9:07:00 13.134 4.523 3.054 2.842 

1/ 31/2013 9:08:00 13.132 4.527 3.001 2.796 

1/ 31/ 2013 9:09:00 13.134 4.527 2.962 2.885 

1/31/2013 9:10:00 13.135 4.526 3.094 3.161 

1/31/2013 9:11:00 13.133 4.527 3.037 3.112 

1/31/2013 9:12:00 13.131 4.533 3.131 3.136 

1/ 31/ 2013 9:13:00 13.114 4.545 3.205 3.077 

1/31/ 2013 9:14:00 13.126 4.542 2.97 3.105 

1/31/2013 9:15:00 13.131 4.54 2.974 3.28 

1/31/2013 9:16:00 17.777 1.795 1.171 1.908 

1/31/2013 9:17:00 13.249 4.536 2.987 2.462 

1/31/2013 9:18:00 13.128 4.548 2.985 3.257 

1/31/ 2013 9:19:00 13.108 4.558 3.072 3.196 

1/ 31/ 2013 9:20:00 13.096 4.569 3.025 3.266 

1/31/2013 9:21:00 13.056 4.591 3.243 3.075 

1/31/2013 9:22:00 13.059 4.592 3.202 3.104 

1/31/2013 9:23:00 13.056 4.598 3.253 3.004 

1/31/ 2013 9:24:00 13.061 4.594 3.149 2.801 

1/ 31/ 2013 9:25:00 13.061 4.594 3.05 2.93 

1/ 31/ 2013 9:26:00 13.065 4.595 3.031 3.407 

1/31/2013 9:27:00 7.715 2.545 1.877 3.677 

1/31/2013 9:28:00 0.146 0.152 0.001 4.393 

1/31/2013 9:29:00 0.122 0.146 -0,015 4.463 

1/ 31/2013 9:30:00 6.5 3.594 -0.012 2.488 

1/ 31/ 2013 9:31:00 rl ~9;;';;:98;;3~---;5-::.1":7~5 --_';;0.':':0::"11;' -{}.283 

1/31/2013 9:32:00 3.862 1.918 2.813 -0.203 

1/31/2013 9:33:00 '"I -0;;;;::12;;3;-.....,;0.;:;.1~5;;.8 --4;::7;;:5;;;2~-"':0:::.1;::5::"'" 

1/31/2013 9:34:00 5.993 2.326 3.991 1.083 

1/ 31/ 2013 9:35:00 13.073 4.574 2.977 4.149 

1/ 31/ 2013 9:36:00 13.105 4.576 2.972 4.347 

1/ 31/ 2013 9:37:00 13.092 4.589 3.059 4.057 

1/31/2013 9:38:00 13.094 4.591 2.943 3.969 

1/31/2013 9:39:00 13.103 4.592 3.263 4.404 

1/31/2013 9:40:00 13.084 4.598 3.124 4.48 

1/ 31/ 2013 9:41:00 13.099 4.598 3.084 4.39 

1/ 31/ 2013 9:42:00 13.09 4.602 3.176 4.227 

1/31/2013 9:43:00 13.089 4.604 3.204 4.366 

1/31/2013 9:44:00 13.084 4.611 3.297 4.566 

1/31/2013 9:45:00 15.255 3.242 2.367 3.895 

1/31/ 2013 9:46:00 18.646 1.511 0.678 0.776 

1/ 31/2013 9:47:00 13.097 4.615 3.053 3.512 

1/ 31/ 2013 9:48:00 13.083 4.62 2.987 3.953 

1/31/2013 9:49:00 13.082 4.627 2.987 3.869 

1/31/2013 9:50:00 13.073 4.634 3.065 3.924 

1/31/2013 9:51:00 13.081 4.635 2.953 4.007 

1/ 31/ 2013 9:52:00 13.077 4.638 2.887 3.975 

1/ 31/ 2013 9:53:00 13.058 4.648 3.088 3.76 

1/31/ 2013 9:54:00 13.08 4.64 2.993 3.968 

0 , 

% 

13.012 

13.006 

13.023 

13.031 

13.034 

13.038 

13.026 

13.032 

13.03 

13.021 

13.002 

12.995 

12.998 

12.997 

12.993 

12.997 

12.991 

12.98 

12.996 

12.999 

12.991 

12.986 

12.988 

12.976 

12.959 

12.943 

12.941 

12.938 

12.948 

12.947 

12.947 

12.954 

12.956 

12.968 

12.97 

12.971 

12.97 

12.971 

12.981 

12.985 

12.993 

12.975 

12.982 

12.972 

12.97 

12.969 

12.965 

12.963 

12.956 

12.954 

12.958 

12.96 

12.972 

12.966 

12.959 

12.961 

12.96 

12.951 

12.962 

NO, 

PPM 

31.944 

32.309 

32.165 

32.066 

31.894 

31.927 

31.984 

32.002 

31.847 

32.303 

32.631 

32.636 

32.614 

32.548 

32.555 

32.453 

32.574 

32.669 

32.344 

32.039 

32.642 

32.393 

32.191 

32.538 

32.612 

33.267 

33.162 

33.269 

33.284 

32.962 

32.555 

32.411 

32.29 

32.208 

32.115 

32.005 

32.179 

32.02 

31.649 

31.595 

31.48 

31.918 

31.743 

31.8 

31.929 

31.812 

31.964 

31.86 

31.859 

31.924 

31.796 

31.829 

31.721 

31.768 

31.684 

31.626 

31.648 

31.959 

31.696 

co 

PPM 

99.181 

94.353 

99.788 

99.539 

102.767 

106.121 

109.258 

108.335 

109.846 

104.818 

99.362 

100.334 

99.974 

102.143 

104.432 

103.05 

104.609 

104.572 

107.131 

115.415 

108.616 

108.876 

114.346 

111.421 

113.825 

102.674 

100.824 

98.771 

96.832 

99.398 

111.686 

114.197 

119.572 

120.D33 

122.251 

124.985 

121.549 

121.44 

129.713 

132.1 

134.913 

127.946 

124.905 

129.546 

127.576 

128.512 

124.424 

127.123 

131.455 

126.375 

128.872 

131.254 

133.151 

130.428 

133.245 

134.775 

134.072 

128.899 

134.578 

THe 

PPM 

18.527 

17.106 

18.559 

18.703 

19.731 

20.3 

21.583 

21.112 

21.684 

20.625 

18.72 

18.821 

18.907 

19.347 

20.721 

19.513 

19.436 

19.332 

20.251 

23.04 

21.63 

21.174 

22.591 

21.773 

22.586 

18.815 

17.837 

17.341 

16.993 

17.47 

20.987 

21.796 

23.468 

24.097 CO bias 

24.354 

25.322 02/C02 bias 

23.584 

23.927 NOx bias 

26.67 

27.655 

28.593 

25.909 

24.168 

26.603 

26.022 

26.118 

24.836 

26.03 

27.44 

25.369 

26.304 

27.104 

27.693 

25.974 

27.235 

28.196 

28.399 

25.984 

28.404 
O2 CO2 NOx CO 

Date Time % % PPM PPM 

1/31/2013 9:55:00 13.063 4.65 3.134 3.927 

1/31/2013 9:56:00 13.077 4.646 3.004 3.799 

1/31/2013 9:57:00 13.458 4.378 2.853 3.788 

1/ 31/2013 9:58:00 20.558 0.252 0.068 1.112 

1/ 31/ 2013 9:59:00 14.589 3.883 2.19 1.873 

1/ 31/2013 10:00:00 13.064 4.655 2.851 3.466 

1/31/ 2013 10:01:00 13.055 4.662 2.772 3.475 

1/31/2013 10:02:00 13.039 4.672 2.867 3.467 

1/31/2013 10:03:00 13.032 4.681 2.839 2.652 

1/31/2013 10:04:00 13.027 4.687 2.79 2.687 

1/31/2013 10:05:00 13.03 4.688 2.848 2.925 

1/31/2013 10:06:00 13.028 4.689 2.882 2.772 

1/ 31/ 2013 10:07:00 13.032 4.691 2.867 2.964 

1/ 31/2013 10:08:00 13.034 4.691 2.895 2.952 

1/ 31/2013 10:09:00 13.635 4.282 2.767 2.533 

1/31/ 2013 10:10:00 20.509 0.321 0.061 0.731 

1/31/2013 10:11:00 16.257 2.94 1.678 1.289 

1/31/2013 10:12:00 13.05 4.698 3.006 3.673 

1/31/2013 10:13:00 13.042 4.704 2.973 3.924 

1/31/2013 10:14:00 13.045 4.707 3.114 3.815 

1/31/2013 10:15:00 13.056 4.706 2.946 3.97 

1/ 31/2013 10:16:00 13.053 4.71 3.07 4.167 

1/31/ 2013 10:17:00 13.055 4.713 3.084 4.277 

1/31/ 2013 10:18:00 13.057 4.714 3.057 3.949 

1/ 31/2013 10:19:00 13.046 4.721 3.013 3.916 

1/31/2013 10:20:00 13.048 4.723 3.01 3.816 

1/31/2013 10:21:00 10.772 4.732 1.68 2.172 

1/31/2013 10:22:001"'1"';9::i'.i97;";4~--;5"'.3:i:O"'7--_iO:;:0~21:-1 -0.284 

1/ 31/2013 10:23:00 8.987 4.727 0.258 -0.386 

1/31/2013 10:24:00 0.229 0.268 4.705 0.002 

1/ 31/ 2013 10:25:001"'1 -0;;;~12:;:1;-""';0';;.2;':;4;;'9 --4';';;':73:;:1~""';0';;1:;;6;;'2"" 

1/31/ 2013 10:26:00 0.12 0.244 2.317 1.401 

1/ 31/2013 10:27:00 0.097 0.242 -0.037 4.329 

1/31/2013 10:28:00 0.095 0.241 -0.041 4.44 

1/31/2013 10:29:00 7.499 2.944 1.627 3.539 

1/31/2013 10:30:00 13.053 4.715 2.995 1.879 

1/31/2013 10:31:00 13.078 4.718 2.967 1.598 

1/ 31/ 2013 10:32:00 13.083 4.724 3.015 1.854 

1/ 31/ 2013 10:33:00 13.096 4.724 2.955 1.753 

1/ 31/2013 10:34:00 13.107 4.722 2.921 1.624 

1/ 31/2013 10:35:00 13.098 4.732 3.02 1.556 

1/ 31/2013 10:36:00 13.123 4.725 3 1.435 

1/31/2013 10:37:00 13.117 4.731 3.108 1.62 

1/31/2013 10:38:00 13.125 4.73 2.957 1.498 

1/31/2013 10:39:00 13.119 4.735 3.047 1.635 

1/ 31/2013 10:40:00 13.124 4.739 2.989 1.766 

1/ 31/ 2013 10:41:00 18.373 1.602 1.022 0.945 

1/31/ 2013 10:42:00 20.487 0.5 0.05 0.135 

1/ 31/2013 10:43:00 13.288 4.722 2.723 0.999 

1/31/2013 10:44:00 13.135 4.739 2.952 1.815 

1/31/2013 10:45:00 13.141 4.74 2.898 1.95 

1/31/2013 10:46:00 13.141 4.742 2.794 2.571 

1/31/2013 10:47:00 13.131 4.749 2.919 3.228 

1/31/2013 10:48:00 13.138 4.748 2.882 3.44 

1/ 31/2013 10:49:00 13.145 4.746 2.822 3.475 

1/ 31/2013 10:50:00 13.143 4.748 2.938 3.527 

1/31/ 2013 10:51:00 13.144 4.749 2.919 3.78 

1/ 31/ 2013 10:52:00 13.134 4.755 3.048 3.673 

1/31/2013 10:53:00 13.138 4.757 2.977 3.454 

0 , 

% 

12.952 

12.959 

12.967 

12.954 

12.948 

12.946 

12.946 

12.946 

12.944 

12.943 

12.94 

12.925 

12.926 

12.943 

12.946 

12.942 

12.928 

12.916 

12.926 

12.929 

12.933 

12.933 

12.941 

12.938 

12.929 

12.922 

12.927 

12.93 

12.934 

12.936 

12.936 

12.945 

12.942 

12.941 

12.939 

12.944 

12.949 

12.945 

12.949 

12.949 

12.953 

12.963 

12.962 

12.966 

12.962 

12.958 

12.952 

12.958 

12.961 

12.976 

12.982 

12.99 

12.981 

12.991 

12.995 

12.989 

12.981 

12.973 

12.983 

NO, 

PPM 

31.823 

31.814 

31.712 

31.951 

32.151 

32.246 

32.15 

32.489 

32.701 

32.456 

32.412 

32.517 

32.429 

32.316 

32.472 

32.51 

32.637 

32.599 

32.449 

32.58 

32.313 

32.199 

32.133 

32.151 

32.236 

32.385 

32.622 

32.658 

32.899 

32.993 

33.114 

33.069 

33.095 

33.368 

33.73 

33.563 

33.822 

33.412 

33.805 

33.771 

33.928 

34.013 

33.789 

33.793 

33.697 

33.584 

33.929 

34.096 

33.748 

33.329 

33.289 

32.325 

32.134 

31.964 

31.858 

32.005 

32.011 

32.37 

32.35 

co 

PPM 

132.994 

130.564 

132.239 

131.345 

125.515 

125.954 

125.576 

124.757 

113.932 

119.131 

124.722 

123.821 

124.836 

126.273 

121.869 

120.343 

118.741 

119.525 

123.859 

120.15 

124.012 

124.868 

128.647 

124.947 

125.453 

124.189 

113.902 

108.858 

101.823 

95.106 

90.984 

87.517 

87.82 

80.19 

70.732 

70.104 

60.772 

69.428 

67.36 

60.212 

57.097 

49.895 

58.242 

55.264 

60.834 

69.242 

57.275 

54.851 

49.515 

67.433 

73.152 

91.757 

110.64 

116.978 

118.058 

118.641 

119.274 

112.812 

110.44 

THe 

PPM 

26.775 

26.544 

27.108 

27.498 

24.203 

24.743 

23.731 

24.305 

21.575 

23.397 

25.198 

24.519 

24.937 

24.515 

23.699 

23.639 

23.535 

23.391 

24.316 

23.491 

24.211 

24.208 

26.385 

25.307 

25.14 

25.191 

21.753 

19.509 02/C02 bias 

18.433 

17.051 

15.718 NOx bias 

14.57 

14.199 

12.537 CO bias 

10.823 

10.808 

8.598 

10.502 

10.278 

8.613 

7.618 

6.169 

8.096 

7.105 

8.556 

10.568 

7.23 

7.356 

5.63 

9.782 

11.477 

15.484 

21.261 

21.477 

22.579 

23.738 

23.615 

21.515 

20.437 
O2 CO2 NOx CO 

Date Time % % PPM PPM 

1/ 31/ 2013 10:54:00 13.131 4.764 2.792 3.242 

1/ 31/ 2013 10:55:00 13.131 4.766 2.818 3.049 

1/ 31/ 2013 10:56:00 13.132 4.764 2.857 2.966 

1/31/2013 10:57:00 16.406 2.861 1.6 1.989 

1/31/2013 10:58:00 13.161 4.763 2.723 2.379 

1/ 31/ 2013 10:59:00 13.138 4.764 2.722 2.651 

1/ 31/ 2013 11:00:00 13.139 4.762 2.704 2.882 

1/ 31/ 2013 11:01:00 13.131 4.773 2.797 2.726 

1/31/ 2013 11:02:00 13.134 4.771 2.788 2.504 

1/31/2013 11:03:00 13.136 4.77 2.666 2.363 

1/31/2013 11:04:00 13.135 4.77 2.819 2.164 

1/ 31/ 2013 11:05:00 13.134 4.773 2.695 2.16 

1/ 31/ 2013 11:06:00 13.133 4.776 2.862 2.062 

1/ 31/ 2013 11:07:00 13.121 4.783 2.986 2.131 

1/31/2013 11:08:00 13.113 4.791 2.875 1.933 

1/31/2013 11:09:00 16.454 2.763 1.703 2.169 

1/31/2013 11:10:00 20.286 0.688 0.098 0.288 

1/ 31/ 2013 11:11:00 13.239 4.76 2.918 2.334 

1/ 31/ 2013 11:12:00 13.141 4.773 2.941 3.226 

1/31/ 2013 11:13:00 13.139 4.773 2.888 3.136 

1/31/2013 11:14:00 13.134 4.777 2.976 3.275 

1/31/2013 11:15:00 13.14 4.774 3.031 3.407 

1/ 31/ 2013 11:16:00 13.133 4.782 3.127 3.205 

1/ 31/ 2013 11:17:00 13.146 4.773 2.974 3.516 

1/ 31/2013 11:18:00 13.155 4.769 3.022 3.391 

1/31/ 2013 11:19:00 13.15 4.771 2.986 3.333 

1/31/2013 11:20:00 13.15 4.773 3.035 3.267 

1/31/2013 11:21:00 4.394 1.611 1.067 3.803 

1/31/ 2013 11:22:00 0.124 0.292 -0.029 4.393 

1/ 31/2013 11:23:00 0.12 0.287 -0.D35 4.453 

1/ 31/ 2013 11:24:00 6.615 3.766 -0.032 2.476 

1/31/2013 11: 25:001r-:1:';0:';0'"31:--;;5';;.3~5;;'6 ---"'0."'0;;33:-' -0.31 

1/31/2013 11:26:00 3.285 1.807 3.034 -0.222 

1/31/2013 11:27:001r-:';0":' .1'"2 --;;0';;2~96~-4'i'. 7~1:-::5--;;0C;.1'"25;::-' 

1/ 31/ 2013 11:28:00 0.109 0.274 1.879 0.085 

1/ 31/ 2013 11:29:001r-"0:;'.0:::9:::4--;;0';;.2::=6:;"3 ---~0~0~32:--;;-0:-:0~2~9" 

1/31/2013 11:30:00 8.113 4.521 3.228 1.85 

1/31/2013 11:31:00 10.049 5.359 4.736 4.374 

1/31/2013 11:32:00· .. 1...:,:;10,:.:0;,;6;;.........:5,;:.'"36;;....-.;.4."74;;3:--"""'4;:;.4"'2.;.4-. 

1/ 31/ 2013 11:33:00 12.291 4.884 3.423 4.001 

1/ 31/ 2013 11:34:00 13.114 4.786 2.922 3.605 

1/ 31/ 2013 11:35:00 13.125 4.782 2.86 3.485 

1/31/2013 11:36:00 13.122 4.782 2.822 3.662 

1/31/2013 11:37:00 13.117 4.786 2.936 3.783 

1/31/ 2013 11:38:00 13.121 4.784 3.017 3.957 

1/ 31/2013 11:39:00 13.115 4.789 3.094 3.992 

1/ 31/ 2013 11:40:00 13.115 4.791 3.09 3.951 

1/31/2013 11:41:00 13.128 4.784 3.008 3.676 

1/31/2013 11:42:00 13.121 4.788 2.956 3.642 

1/31/2013 11:43:00 13.116 4.79 2.988 3.569 

1/ 31/ 2013 11:44:00 18.281 1.724 1.009 2.146 

1/ 31/ 2013 11:45:00 16.095 3.136 1.655 1.407 

1/ 31/ 2013 11:46:00 13.131 4.78 2.881 3.62 

1/31/2013 11:47:00 13.119 4.794 2.944 3.61 

1/31/2013 11:48:00 13.12 4.794 2.869 3.596 

1/31/ 2013 11:49:00 13.112 4.796 2.948 3.882 

1/ 31/ 2013 11:50:00 13.108 4.798 2.956 3.866 

1/ 31/ 2013 11:51:00 13.107 4.8 3.02 4.029 

1/31/2013 11:52:00 13.094 4.807 3.034 3.599 

0, 

% 

12.981 

12.982 

12.987 

12.976 

12.989 

12.994 

12.996 

12.983 

12.994 

12.996 

13.002 

12.995 

12.995 

12.985 

12.968 

12.97 

12.967 

12.969 

12.977 

12.981 

12.976 

12.982 

12.96 

12.979 

12.988 

12.991 

12.984 

12.991 

12.989 

12.986 

12.975 

12.979 

12.972 

12.958 

12.969 

12.981 

12.984 

12.979 

12.965 

12.97 

12.974 

12.981 

12.982 

12.975 

12.975 

12.97 

12.964 

12.976 

12.977 

12.969 

12.985 

12.986 

12.989 

12.976 

12.975 

12.968 

12.965 

12.968 

12.953 

NO, 

PPM 

32.391 

32.383 

32.494 

32.52 

32.353 

32.241 

32.026 

32.388 

32.355 

32.138 

32.011 

31.966 

32. 114 

32.183 

32.46 

32.098 

32.719 

32.743 

32.548 

32.434 

32.425 

32.603 

32.897 

32.505 

32.289 

32.44 

32.425 

32.459 

32.352 

32. 36 

32.533 

32.442 

32.427 

32.928 

32.45 

32.209 

32.372 

32.239 

32.501 

32.148 

32.21 

32.238 

31.949 

32.065 

32.095 

32.34 

32.404 

32.202 

32.161 

32.468 

31.97 

32.194 

32.215 

32.495 

32.472 

32.329 

32.425 

32.556 

32.801 

co 

PPM 

110.928 

109.835 

107.266 

105.603 

107.977 

107.204 

116.261 

111.56 

109.53 

110.24 

113.125 

110.974 

112.426 

113.288 

109.188 

119.526 

107.351 

105.43 

108.742 

109.41 

114.052 

109.837 

103.683 

109.482 

112.854 

115.663 

114.65 

114.027 

115.994 

114.232 

113.687 

115.081 

117.689 

108.039 

116.288 

118.581 

118.877 

120.026 

122.139 

119.583 

119.099 

117.043 

123.843 

126.094 

125.155 

122.587 

120.446 

120.131 

120.189 

120.816 

125.312 

123.246 

121.513 

119.002 

116.785 

121.442 

119.191 

123.173 

111.824 

THe 

PPM 

21.004 

20.719 

20.066 

19.621 

19.556 

19.686 

22.63 

21.226 

20.682 

20.394 

21.465 

21.218 

22.23 

21.632 

20.148 

23.752 

19.892 

18.666 

19.899 

20 

21.763 

20.632 

18.234 

19.717 

21.248 

22.317 

22.078 

21.681 

21.58 

20.807 CO bias 

21.186 

21.976 02/C02 bias 

22.346 

18.636 NOx bias 

21.973 

22.559 Direct Zero 

23.142 

22.142 

24.163 Span Direct 

23.567 

22.94 

22.475 

23.528 

25.207 

24.912 

24.049 

23.823 

23.75 

22.241 

23.467 

24.135 

23.263 

23.874 

23.461 

21.618 

23.109 

22.492 

24.556 

20.672 
Oz COz NO. CO 

Date Time % % PPM PPM 

1/31/2013 11:53:00 13.092 4.809 2.884 3.552 

1/31/2013 11:54:00 13.082 4.814 2.844 3.489 

1/31/2013 11:55:00 13.077 4.818 2.931 3.514 

1/ 31/2013 11:56:00 16.326 2.919 1.594 2.358 

1/31/2013 11:57:00 13.129 4.802 2.679 2.732 

1/31/2013 11:58:00 13.083 4.813 2.772 3.279 

1/ 31/ 2013 11:59:00 13.069 4.825 2.801 2.95 

1/31/ 2013 12:00:00 13.076 4.82 2.727 2.979 

1/ 31/2013 12:01:00 13.058 4.828 2.902 2.563 

1/31/2013 12:02:00 13.069 4.822 2.835 2.31 

1/31/2013 12:03:00 13.051 4.831 2.923 2.11 

1/31/2013 12:04:00 13.056 4.828 2.804 2.371 

1/31/ 2013 12:05:00 13.056 4.829 2.868 2.323 

1/31/ 2013 12:06:00 13.058 4.824 2.905 2.208 

1/31/2013 12:07:00 17.457 2.204 1.367 1.491 

1/31/ 2013 12:08:00 20.76 0.364 ·0.012 0.174 

1/31/2013 12:09:00 16.277 3.029 1.608 1.275 

1/31/2013 12:10:00 13.107 4.798 2.883 3.502 

1/31/2013 12:11:00 13.094 4.806 2.884 3.388 

1/31/2013 12:12:00 13.103 4.802 2.842 3.726 

1/31/ 2013 12:13:00 13.104 4.804 3.044 3.993 

1/ 31/2013 12:14:00 13.105 4.804 2.969 3.97 

1/31/2013 12:15:00 13.103 4.806 2.999 4.079 

1/ 31/ 2013 12:16:00 13.106 4.804 2.953 3.706 

1/ 31/2013 12:17:00 13.1 4.807 2.837 3.484 

1/31/2013 12:18:00 13.104 4.807 2.977 3.136 

1/31/2013 12:19:00 10,42 3.765 2.706 3.36 

1/31/2013 12:20:00 0.168 0.322 ·0.022 4.197 

1/31/2013 12:21:00 0.12 0.311 ·0.033 4.43 

1/31/2013 12:22:00 7.383 4.175 -0.03 2.007 

1/31/2013 12:23:00 .. '""'1;,;0::,; .00:,;:2:,--::5.:;.3"'8""3--.""0"' .0:,::37.-. -0.354 

1/31/2013 12:24:00 8.605 4.597 0.408 -0.387 

1/31/2013 12:25:00 0.181 0.332 4.704 0.036 

1/31/ 2013 12: 26:oor"' -';;0-;1'i2'---;O:-i.3~174 --::-4.'71;;9:---;O-;.1:i;6'2-' 

1/31/2013 12:27:00 8.728 3.487 3.602 1.425 

1/31/2013 12:28:00 13.032 4.822 2.879 3.227 

1/ 31/2013 12:29:00 13.047 4.826 2.948 3.287 

1/ 31/ 2013 12:30:00 13.056 4.826 2.908 3.253 

1/ 31/ 2013 12:31:00 13.056 4.828 2.89 3.181 

1/ 31/2013 12:32:00 13.057 4.827 2.893 3.114 

1/31/2013 12:33:00 13.058 4.828 2.87 3.652 

1/31/2013 12:34:00 13.05 4.832 3.041 3.504 

1/31/2013 12:35:00 13.062 4.826 3.048 3.346 

1/31/2013 12:36:00 13.064 4.826 3.048 3.462 

1/31/2013 12:37:00 13.07 4.824 3.004 2.987 

1/31/2013 12:38:00 13.074 4.823 2.932 3.122 

1/31/ 2013 12:39:00 13.069 4.826 2.95 3.622 

1/ 31/ 2013 12:40:00 17.426 2.171 1.436 2.044 

1/31/ 2013 12:41:00 16.443 2.985 1.471 1.097 

1/ 31/ 2013 12:42 :00 13.057 4.833 2.933 3.226 

1/31/2013 12:43:00 13.052 4.837 2.931 3.263 

1/31/2013 12:44:00 13.045 4.84 2.959 3.145 

1/31/2013 12:45:00 13.047 4.842 3.041 2.947 

1/31/2013 12:46:00 13.063 4.832 2.803 3.18 

1/31/2013 12:47:00 13.054 4.837 2.92 3.186 

1/ 31/2013 12:48:00 13.055 4.835 2.845 3.174 

1/ 31/ 2013 12:49:00 13.054 4.836 2.786 3.283 

1/ 31/2013 12:50:00 13.062 4.83 2.806 3.38 

1/31/2013 12:51:00 16.429 2.749 1.716 2.579 

0 , 

% 

12.959 

12.953 

12.948 

12.949 

12.963 

12.957 

12.944 

12.945 

12.945 

12.952 

12.936 

12.943 

12.939 

12.945 

12.945 

12.944 

12.944 

12.947 

12.945 

12.954 

12.945 

12.945 

12.947 

12.946 

12.948 

12.945 

12.948 

12.945 

12.954 

12.949 

12.947 

12.946 

12.948 

12.924 

12.945 

12.946 

12.954 

12.948 

12.952 

12.952 

12.954 

12.945 

12.948 

12.953 

12.958 

12.956 

12.961 

12.955 

12.955 

12.953 

12.95 

12.949 

12.945 

12.965 

12.956 

12.959 

12.956 

12.963 

12.943 

NO, 

PPM 

32.655 

32.583 

32.723 

32.563 

32.248 

32.226 

32.679 

32.739 

32.829 

32.705 

33.198 

32.761 

32.981 

32.928 

32.977 

32.677 

32.804 

32.522 

32.579 

32.187 

32.355 

32.266 

32.292 

32.412 

32.593 

32.852 

32.557 

32.693 

32.749 

32.611 

32.548 

32.739 

32.768 

33.143 

33.004 

32.821 

32.613 

32.693 

32.871 

32.763 

32.309 

32.812 

32.845 

32.732 

33.057 

32.539 

32.632 

32.734 

32.485 

32.375 

32.682 

32.705 

32.872 

32.341 

32.508 

32.416 

32.388 

32.19 

32.862 

co 

PPM 

114.384 

117.281 

117.105 

116.082 

119.959 

124.63 

117.2 

116.117 

112.413 

~13.492 

107.471 

112.684 

113.298 

111.926 

109,078 

111.652 

114.708 

116.513 

114.756 

121.07 

123.923 

122.914 

123.361 

121.746 

117.124 

112.036 

112.944 

117.904 

108.191 

113.413 

116.099 

112.711 

112.108 

108.761 

103.458 

108.572 

109.805 

111.139 

109.037 

107.009 

118.264 

115.325 

110.847 

112.407 

104.874 

110.519 

119.572 

111.061 

116.102 

121.268 

119.328 

115.778 

111.794 

118.823 

120.157 

121.207 

123.322 

124.852 

119.007 

THe 

PPM 

21.578 

22.672 

22.323 

21.173 

22.544 

24.365 

21.741 

21.692 

20.95 

21.152 

19.805 

20.56 

20.714 

20.898 

20.459 

20.375 

21.554 

23.042 

22.111 

23.075 

24.256 

23.323 

24.398 

24.236 

22.326 

20.933 

21.073 

23.218 

19.549 CO bias 

20.643 

22.31 02/C02 bias 

21.637 

20.594 

21.191 NOx bias 

18.147 

19.587 

19.603 

19.864 

19.106 

18.708 

22.425 

20.8 

19.703 

20.04 

18.622 

19.565 

21.966 

19.833 

20.824 

21.995 

22.603 

21.494 

20.012 

22.124 

22.636 

22.622 

22.324 

23.216 

22.305 
O2 CO2 NO. CO 

Date Time % % PPM PPM 

1/31/2013 12:52:00 14.61 4.048 2.107 2.125 

1/31/2013 12:53:00 13.032 4.846 2.921 3.606 

1/31/2013 12:54:00 13.034 4.846 2.942 3.504 

1/31/2013 12:55:00 13.032 4.849 3.073 3.262 

1/31/ 2013 12:56:00 13.033 4.847 2.944 3.02 

1/31/2013 12:57:00 13.046 4.839 3.027 3.354 

1/31/ 2013 12:58:00 13.046 4.841 2.969 3.771 

1/31/2013 12:59:00 13.041 4.844 3.056 3.407 

1/31/2013 13:00:00 13.035 4.848 2.92 3.533 

1/31/2013 13:01:00 13.032 4.851 2.889 3.11 

1/31/2013 13:02:00 13.028 4.857 2.896 3.123 

1/31/2013 13:03:00 16.121 3.041 1.656 2.233 

1/ 31/2013 13:04:00 13.05 4.859 2.872 2.378 

1/ 31/ 2013 13:05:00 13.014 4.867 2.804 2.695 

1/ 31/ 2013 13:06:00 13.023 4.866 2.793 2.753 

1/31/2013 13:07:00 13.019 4.868 2.741 2.851 

1/31/2013 13:08:00 13.026 4.866 2.676 3.2 

1/31/2013 13:09:00 13.028 4.865 2.831 2.897 

1/31/2013 13:10:00 13.005 4.885 2.933 2.484 

1/31/2013 13:11:00 13.007 4.889 2.964 2.236 

1/31/2013 13:12:00 13.006 4.889 2.972 2.332 

1/31/2013 13:13:00 13.011 4.882 2.94 2.059 

1/31/2013 13:14:00 13.012 4.882 2.818 2.201 

1/ 31/ 2013 13:15:00 13.013 4.882 2.813 2.091 

1/31/2013 13:16:00 11.339 4.785 2.053 2.042 

1/31/2013 13:17:00 9.987 5.425 -0.01 -0.252 

1/31/2013 13:18:00'"1 ""9;;;.;;;98,;7,.........;5-:.4"3::-1---"'0".0;,:;25,..., -0.388 

1/31/2013 13:19:00 4.017 2.222 2.657 -0.219 

1/31/2013 13:20:00'"1 ""0~.::-12~4-....;0".3;;:5::-6 --4::-.,;;72~4,.....~0~1::,:38~ 

1/ 31/2013 13:21:00 0.118 0.348 2.587 1.262 

1/31/ 2013 13:22:00 0.118 0.345 -0.031 4.334 

1/ 31/ 2013 13:23:00 0.095 0.342 -0,038 4.434 

1/31/2013 13:24:00 9.248 0.353 -0.027 2.407 

1/31/2013 13:25 001.....,0;;;.::-12;;;3-....;0"3~1::-5 ---"'0.;'0'"37:--"";0':';.0;'5::-3 -, 

1/31/2013 13:26:00 6.136 3.592 2.332 1.174 

1/31/2013 13:27:00 10.01 5.425 4.747 4.352 

1/31/2013 13:28 001'--:1;;;0';;0';'13;---;:5":.4;;;25~-4::'~74:':8"""--:4-:4;;;3::-1-' 

1/31/2013 13:29:00 18.081 1.128 1.453 2.714 

1/31/ 2013 13:30:00 20.722 0.316 -0.026 0.308 

1/31/2013 13:31:00 20.73 0,035 -0.026 0.163 

1/31/2013 13:32:00 20.735 -0.006 -0.028 0.131 

1/31/2013 13:33:00 20.736 -0.006 -0.029 0.135 

1/31/2013 13:34:00 20.735 8.137 -0.029 0.127 

1/31/2013 13:35:00 20.735 9.603 -0.026 0.136 

1/31/2013 13:36:00 20.741 9.613 -0.032 0.132 

1/ 31/2013 13:37:00 20.746 9.572 -0.033 0.126 

1/ 31/2013 13:38:00 20.746 9.537 -0.036 0.121 

1/31/ 2013 13:39:00 20.746 9.505 -0.033 0.114 

1/ 31/2013 13:40:00 20.744 7.926 -0.031 0.111 

1/31/2013 13:41:00 20.75 5.111 -0.033 0.112 

1/31/2013 13:42:00 20.753 5.109 -0.029 0.13 

1/31/2013 13:43:00 20.76 5.109 -0,028 0.124 

1/31/2013 13:44:00 20.759 5.763 -0.034 0.102 

1/31/2013 13:45:00 20.763 ..... :,;9.,;;66:;;9:...., -0,038 0.115 

1/31/2013 13:46:00 20.766 1-;.9.:,:.6;:,7,...... -0.039 0.108 

1/31/2013 13:47:00 20.77 6.247 -0.037 0.107 

1/31/2013 13:48:00 20.765 1-::-5'",08~5:-1 -0.032 0.113 

1/31/2013 13:49:00 13.561 4.864 2.486 1.249 

1/31/2013 13:50:00 13.021 4.543 2.841 1.873 

0 , 

% 

12.943 

12.942 

12.94 

12.94 

12.944 

12.947 

12.941 

12.943 

12.944 

12.944 

12.937 

12.939 

12.915 

12.936 

12.94 

12.941 

12.944 

12.948 

12.929 

12.927 

12.915 

12.929 

12.925 

12.937 

12.92 

12.924 

12.936 

12.914 

12.919 

12.903 

12.934 

12.927 

12.914 

12.928 

12.932 

12.933 

12.928 

12.899 

12.915 

12.906 

12.927 

12.938 

12.922 

12.907 

12.918 

12.922 

12.904 

12.901 

12.871 

12.885 

12.89 

12.899 

12.896 

12.888 

12.9 

12.898 

12.895 

12.89 

12.888 

NO, 

PPM 

32.841 

32.967 

33.093 

33.35 

33.262 

32.939 

32.893 

32.979 

32.792 

33.008 

33.207 

32.903 

33.291 

33.149 

33.075 

32.892 

32.63 

32.638 

33.212 

33.1 

33.134 

33.066 

33.103 

32.847 

32.936 

32.94 

32.781 

33.045 

32.675 

33.004 

32.627 

32.847 

32.96 

33.187 

32.639 

32.839 

32.723 

33.313 

32.746 

33.022 

33.026 

32.773 

33.076 

33.279 

33.362 

33.215 

33.665 

33.905 

34.424 

33.822 

33.647 

33.508 

33.771 

33.897 

33.666 

33.765 

33.704 

33.95 

34.147 

co 

PPM 

117.361 

114.642 

112.627 

107.448 

102.424 

107.213 

115.862 

104.867 

113.164 

106.441 

104.398 

106.624 

105.995 

102.789 

107.249 

108.166 

116.596 

112.531 

109.1 

106.18 

106.601 

104.894 

106.315 

105.32 

112.874 

107.754 

106.751 

109.495 

108.902 

107.134 

114.172 

112.723 

111.122 

103.13 

111.188 

112.261 

115.377 

102.448 

109.34 

109.652 

105.992 

108.305 

108.063 

103.687 

99.973 

107.042 

100.669 

96.728 

89.293 

90.124 

92.004 

91.478 

87.142 

87.133 

91.024 

90.791 

94.335 

92.218 

86.149 

THC 

PPM 

21.224 

20.39 

19.792 

19.045 

17.839 

19.02 

21.901 

18.391 

19.974 

18.197 

18.254 

18.883 

18.769 

18.005 

19.162 

18.944 

20.323 

19.972 

19.884 

18.555 

18.846 

17.793 

18.356 

18.094 

20.968 

19.139 

18.462 02/C02 bias 

19.236 

19.234 NOx bias 

18.534 

20.357 

20.388 CO bias 

19.36 

17.577 Direct Zero 

20.374 

19.964 

21.445 Direct Span 

17.703 

19.856 

19.105 

18.332 

18.975 C02 Cal Zero 

19.442 

17.812 

16.975 

18.496 

16.93 

16.5 

14.493 

14.5 

14.252 

14.995 

13.267 

13.76 

14.81 C02 Cal High 

14.867 

15.7 C02 Mid 

15.012 

13.325 
~ ~ N~ m ~ N~ m 

Date Time % % PPM PPM % PPM PPM 

1/31/2013 13:51:00 13.016 4.547 2.769 1.967 12.879 34.147 87.157 

1/31/2013 13:52:00 13.013 4.548 2.828 1.972 12.886 34.017 89.321 

1/31/2013 13:53:00 13.016 4.549 2.821 2.004 12.89 34.22 87.036 

1/31/2013 13:54:00 13.014 4.551 2.829 1.848 12.886 34.143 85.563 

1/31/2013 13:55:00 13.012 4.551 2.78 1.83 12.885 34.387 81.383 

1/31/2013 13:56:00 13.012 4.557 2.758 1.796 12.884 34.302 80.254 

1/31/2013 13:57:00 13.014 4.554 2.746 1.808 12.891 34.266 81.11 

1/31/2013 13:58:00 13.021 4.551 2.674 1.972 12.899 33.795 87.379 

1/31/2013 13:59:00 13.015 4.554 2.77 1.961 12.892 34.125 85.903 

1/31/2013 14:00:00 13.028 4.54 2.769 1.844 12.951 33.78 81.344 

1/31/2013 14:01:00 1.702 0.681 0.521 0.744 4.189 12.375 48.309 

1/31/2013 14:02:00r-~0';;.09~6;.....~0:;;.0:::0:;,7_~-:;;0~.0~36;-.....::-0~.04~9 __ 0~.;;.02;;8;.....~0~.3:::6;9 __ 0:;;'.;94;8:-, 

1/31/2013 14:03 :00LI....::0~.0.::.93=-_:::.0.~0:::.07:.........;-~0;::.0::3.:.7_~-~0;::.0::3:::.8 _...;0::;.:::.02;:2:..........:0:::..2~8:::9:.....--=-o:::..~2:;24:.J 1/31/2013 14:04:00 7.197 3.763 2.656 1.572 5.198 9.519 11.157 

1/31/2013 14:05:00 10.014 5.096 4.744 4.366 9.936 22.586 124.097 

1/31/2013 14:06:oo"I"';1~0:;;.0:;2;'3 -..;5:;:.0;;9;;.7-....;4.;73;;9;.........:4;;;.4:;:2:::.8--9;;:.;;.93;:;9:.........;24~.3;4:;:9:......:.1;:34;'::.2:;;9;';'9"1 

1/31/2013 14:07:00 11.358 4.527 2.93 3.391 11.318 21.481 101.822 

1/31/2013 14:08:oo ..... .::.9.:.::9::.82=--_...;5::;.;1 __ -~0;::.0~2:.4... -0.018 9.921 1.915 17.03 

1/31/2013 14:09:00LI....::;9.;:98::;:5:..........:5:;.:.1::;0.;.7 __ -o.;:;.0;:,31~ -0.403 9.913 1.197 -0.416 

1/31/2013 14: 10:00 ..... .::3.:.::9:::.07:....._~1.:::8:;87:....._.:;2.;7;13;:........;-o.;:;.:.2:.::3::.3 _~4;:.0:;:6:::7_~1.::3.;;7.:;88::....--=-0::;.~26;;:6;.., 

1/31/2013 14: l1:ooI L....::O:..:.1~2_.....:0::;.0:::5:..._4:.; . .:.72~9:..........:0:;;.1~1::.8 __ 0:::.::.044::...._.:;24::..9:::64::.........:-::.0.~1.:.;73::...J 

1/31/2013 14:12:00 0.116 0.043 2.288 1.453 0.022 10.975 36.975 

1/31/2013 14:13:00 0.108 0.04 -0.036 4.323 0.019 0.843 132.579 

1/31/2013 14:14:00 0.092 0.04 -0.04 4.431 0.018 0.745 1 134.402 1 

1/31/2013 14:15:00 9.759 3.382 1.829 2.549 8.903 18.03 107.891 

1/31/2013 14:16:00 13.265 4.395 2.561 0.59 13.236 29.591 51.999 

1/31/2013 14:17:00 13.274 4.403 2.822 0.513 13.228 30.016 50.046 

1/31/2013 14:18:00 13.276 4.406 2.65 0.514 13.228 30.44 46.391 

1/31/2013 14:19:00 13.288 4.403 2.589 0.471 13.245 30.587 44.649 

1/31/2013 14:20:00 13.279 4.409 2.699 0.478 13.237 30.593 45.885 

1/31/2013 14:21:00 13.274 4.416 2.827 0.518 13.241 30.648 48.88 

1/31/2013 14:22:00 13.275 4.417 2.819 0.504 13.231 30.706 47.865 

1/31/2013 14:23:00 13.275 4.422 2.846 0.464 13.226 31.014 45.962 

1/31/2013 14:24:00 13.253 4.436 2.95 0.39 13.24 30.842 45.429 

1/31/2013 14:25:00 13.256 

1/31/2013 14:26:00 13.243 

1/31/2013 14:27:00 13.268 

1/31/2013 14:28:00 13.301 

1/31/2013 14:29:00 13.292 

1/31/2013 14:30:00 13.275 

1/31/2013 14:31:00 13.273 

1/31/2013 14:32:00 13.266 

1/31/2013 14:33:00 15.976 

1/31/2013 14:34:00 16.902 

1/31/2013 14:35:00 13.321 

1/31/2013 14:36:00 13.309 

1/31/2013 14:37:00 13.308 

1/31/2013 14:38:00 13.318 

1/31/2013 14:39:00 13.313 

1/31/2013 14:40:00 13.319 

1/31/2013 14:41:00 13.297 

1/31/2013 14:42:00 13.3 

1/31/2013 14:43:00 13.307 

1/31/2013 14:44:00 13.294 

1/31/2013 14:45:00 13.299 

1/31/2013 14:46:00 13.289 

1/31/2013 14:47:00 13.267 

1/31/2013 14:48:00 13.263 

1/31/2013 14:49:00 13.265 

4.436 2.748 0.371 13.24 30.992 45.342 

4.444 3.002 0.343 13.247 31.006 44.584 

4.433 2.701 0.339 13.272 30.279 46.107 

4.414 2.765 0.472 13.295 29.912 55.232 

4.422 2.748 0.442 13.284 29.958 54.945 

4.438 2.941 0.375 13.251 30.698 48.523 

4.438 2.678 0.335 13.269 30.424 46.197 

4.443 2.903 0.352 13.234 30.662 47.113 

2.766 1.997 0.322 13.24 30.625 47.311 

2.419 1.269 0.211 13.249 30.501 46.582 

4.413 2.754 0.635 13.235 30.635 47.908 

4.42 2.769 0.648 13.223 30.67 47.142 

4.421 2.838 0.698 13.235 30.393 49.647 

4.417 2.632 0.706 13.235 30.611 49.991 

4.421 2.641 0.624 13.238 30.485 46.614 

4.42 2.68 0.729 13.257 30.3 51.401 

4.434 2.77 0.709 13.223 30.692 49.806 

4.435 2.804 0.707 13.227 30.713 47.554 

4.429 2.72 0.717 13.26 30.499 48.824 

4.441 2.807 0.68 13.218 30.896 46.986 

4.438 2.756 0.676 13.242 30.753 46.777 

4.445 2.761 0.622 13.238 30.867 45.424 

4.463 2.918 0.56 13.227 30.879 44.823 

4.465 2.861 0.592 13.219 30.773 47.842 

4.463 2.835 0.574 13.207 30.944 48.253 

THe 

PPM 

13.144 

13.91 

13.89 

13.197 

12.294 

11.209 

11.389 

13.627 

13.744 

12.215 

8.292 

5.669 

5.204 

5.685 

5.562 

6.73 

5.722 

1.163 

-0.02 

-0.02 

-0.021 

-0.018 

-0.Q15 

-0.015 

1.463 

6.397 

5.957 

5.201 

4.864 

4.973 

5.845 

5.594 

4.959 

4.919 

5.082 

4.806 

4.67 

7.181 

6.807 

5.862 

4.919 

4.881 

4.761 

4.903 

5.403 

4.943 

5.756 

5.751 

4.975 

5.928 

5.663 

5.184 

5.425 

4.993 

5.Q38 

4.818 

4.615 

5.389 

5.537 

Direct Zero 

Span Direct 

02/C02 bias 

NOx bias 

CO bias 
~ ~ ~ ro ~ N~ ro 

Date Time % % PPM PPM % PPM PPM 

1/31/2013 14:50:00 13.272 4.459 2.732 0.555 13.248 30.725 46.027 

1/ 31/ 2013 14:51:00 15.738 2.927 1.948 0.502 13.235 30.855 45.795 

1/ 31/ 2013 14:52:00 13.751 4.27 2.514 0.336 13.27 30.613 45.495 

1/31/2013 14:53:00 13.294 4.446 2.886 0.532 13.231 30.785 46.523 

1/31/2013 14:54:00 13.299 4.442 2.898 0.511 13.269 30.706 45.481 

1/31/2013 14:55:00 13.306 4.436 3.195 0.525 13.282 30.49 47.183 

1/ 31/ 2013 14:56:00 13.307 4.435 2.923 0.551 13.274 30.72 48.821 

1/ 31/ 2013 14:57:00 13.302 4.438 2.953 0.498 13.266 30.784 44.861 

1/ 31/ 2013 14:58:00 13.304 4.436 2.846 0.539 13.276 30.654 47.165 

1/31/2013 14:59:00 13.31 4.432 2.877 0.512 13.285 30.66 46.003 

1/31/2013 15:00:00 13.306 4.435 2.906 0.516 13.29 30.492 46.671 

1/ 31/ 2013 15:01:00 13.307 4.435 4.427 0.491 13.281 30.554 45.909 

1/ 31/ 2013 15:02:00 13.309 4.435 5 0.462 13.287 30.518 45.025 

1/ 31/ 2013 15:03:00 13.301 4.442 5 0.482 13.283 30.403 47.217 

1/31/2013 15:04:00 13.3 4.446 4.78 0.491 13.278 30.509 46.878 

1/31/2013 15:05:00 13.277 4.459 4.633 0.401 13.243 31.146 42.023 

1/31/2013 15:06:00 13.278 4.455 2.327 0.415 13.26 30.963 41.422 

1/ 31/ 2013 15:07:00 13.276 4.456 2.099 0.437 13.242 31.006 42.115 

1/ 31/ 2013 15:08:00 13.274 4.459 2.191 0.425 13.212 31.118 41.332 

1/ 31/2013 15:09:00 13.289 4.448 2.175 0.475 13.248 30.604 44.198 

1/31/2013 15:10:00 13.287 4.448 2.021 0.588 13.257 30.17 50.633 

1/31/2013 15:11:00 13.313 4.431 1.912 0.674 13.291 29.824 55.295 

1/31/2013 15:12:00 13.258 4.463 2.062 0.52 13.247 31.016 45.723 

1/ 31/ 2013 15:13:00 13.357 4.404 1.798 1.219 13.314 28.219 90.907 

1/ 31/ 2013 15:14:00 13.299 4.443 1.915 0.629 13.295 29.948 52.316 

1/31/2013 15:15:00 13.301 4.446 1.909 0.628 13.271 30.385 51.57 

1/31/2013 15:16:00 13.305 4.443 1.962 0.681 13.269 29.608 57.438 

1/31/2013 15:17:00 13.283 4.461 2.062 0.554 13.25 30.747 47.221 

1/ 31/ 2013 15:18:00 13.295 4.454 2.04 0.535 13.256 30.345 46.558 

1/31/ 2013 15:19:00 13.293 4.457 2.016 0.55 13.26 30.484 47.036 

1/ 31/ 2013 15:20:00 13.277 4.466 2.1 0.507 13.242 30.805 43.775 

1/31/ 2013 15:21:00 13.279 4.467 2.125 0.505 13.247 30.664 44.014 

1/31/2013 15:22:00 13.276 4.471 3.417 0.517 13.224 30.752 45.618 

1/ 31/ 2013 15:23:00 13.284 4.47 5 0.488 13.257 30.487 46.083 

1/ 31/ 2013 15:24:00 13.276 4.478 4.815 0.489 13.231 30.78 45.811 

1/ 31/ 2013 15:25:00 13.29 4.473 4.717 0.515 13.251 30.444 46.984 

1/31/2013 15:26:00 13.295 4.474 5 0.521 13.254 30.289 49.108 

1/31/2013 15:27:00 13.287 4.479 5 0.528 13.24 30.544 48.328 

1/31/2013 15:28:00 13.301 4.475 5 0.517 13.267 30.443 48.042 

1/ 31/ 2013 15:29:00 13.298 4.48 5 0.47 13.251 30.676 44.848 

1/ 31/ 2013 15:30:00 13.296 4.479 5 0.463 13.262 30.471 44.911 

1/ 31/ 2013 15:31:00 13.291 4.484 5 0.513 13.269 30.182 48.563 

1/31/2013 15:32:00 13.301 4.479 5 0.57 13.291 29.95 51.811 

1/31/2013 15:33:00 13.292 4.483 5 0.521 13.249 30.472 48.52 

1/31/ 2013 15:34:00 13.295 4.484 5 0.488 13.278 30.238 46.993 

1/ 31/ 2013 15:35:00 13.298 4.482 5 0.497 13.275 30.206 47.468 

1/ 31/ 2013 15:36:00 13.3 4.48 5 0.508 13.288 30.071 48.936 

1/ 31/ 2013 15:37:00 13.278 4.496 5 0.474 13.247 30.629 45.683 

1/31/2013 15:38:00 13.291 4.484 5 0.455 13.277 30.287 45.683 

1/31/2013 15:39:00 13.279 4.489 5 0.476 13.26 30.438 46.732 

1/ 31/ 2013 15:40:00 13.281 4.49 5 0.452 13.255 30.566 45.065 

1/ 31/ 2013 15.41:00 13.29 4.486 5 0.488 13.266 30.31 47.314 

1/ 31/ 2013 15:42:00 13.296 4.484 5 0.483 13.272 30.317 47.577 

1/31/ 2013 15:43:00 13.233 4.483 5 0.494 13.271 30.279 48.094 

1/31/2013 15:44:00 0.742 0.357 1.574 0.177 4.221 12.805 36.639 

1/31/ 2013 15:45:00 0.093 0.089 0.072 -0.089 0.028 0.285 1.056 

1/ 31/2013 15:46:00rl ~0i:'0:::;9;';2:---;;0-::0;i:87':--'::0'::0~4'---:-0:':0':i6~5-~0i:'0::;2;';2:---;;0;'; .2~2':---o~;':2~25:-' 

1/ 31/ 2013 15:47:00 14.81 8.158 3.493 4.073 11.217 21.444 50.962 

1/ 31/ 2013 15:48:00 18.784 9.796 4.753 9.297 18.759 48.93 224.876 

THe 

PPM 

4.978 

4.876 

4.72 

4.93 

4.534 

4.837 

5.656 

4.69 

5.105 

4.696 

5.048 

4.762 

4.587 

5.125 

4.837 

3.885 

3.743 

4.03 

3.949 

4.456 

5.555 

6.984 

4.857 

19.971 

6.056 

6. 117 

7.959 

4.998 

4.947 

5.045 

4.364 

4.617 

4.744 

5.096 

4.694 

4.886 

5.7 

5.412 

5.19 

4.504 

4.364 

4.938 

5.867 

5.346 

4.961 

5.03 

5.416 

4.54 

4.643 

4.836 

4.617 

5.064 

5.078 

5.15 

4.75 

4.49 

4.594 

4.463 

4.907 

Cal Zero 
0, 

Date Time % 

1/31/2013 15:49:001 18.794 

1/31/2013 15:50:00 11.242 

1/31/2013 15:51:001 10.036 

1/31/2013 15:52:00 10.036 

1/31/2013 15:53:00 9.986 

1/31/2013 15:54:00 9.976 

1/31/2013 15:55:00 9.977 

1/31/2013 15:56:00 9.982 

1/31/2013 15:57:00 9.986 

1/31/2013 15:58:00 9.985 

1/31/2013 15:59:00 9.987 

1/31/2013 16:00:00 9.999 

1/31/2013 16:01:00 10.011 

1/31/2013 16:02:00 10.011 

1/31/2013 16:03:00 10.029 

1/31/2013 16:04:00 10.036 

1/31/2013 16:05:00 10.038 

1/31/2013 16:06:00 6.375 

1/31/2013 16:06:20 9.248 

1/31/2013 16:06:30 9.261 

1/31/2013 16:06:40 11.181 

1/31/2013 16:06:50 14.656 

1/31/2013 16:07:00 14.883 

1/31/2013 16:07:10 14.916 

1/31/2013 16:07:201 14.935 

1/31/2013 16:07:30 14.121 

1/31/2013 16:07:40 11.452 

1/31/2013 16:07:50 11.172 

1/31/2013 16:08:00 11.131 

1/31/2013 16:08:10 11.124 

1/31/2013 16:08:20 11.124 

1/31/2013 16:08:30 11.121 

1/31/2013 16:08:40 11.259 

1/31/2013 16:08:50 12.857 

1/31/2013 16:09:00 14.939 

1/31/2013 16:09:10 15.106 

1/31/2013 16:09:20 15.135 

1/31/2013 16:09:301 15.137 

1/31/2013 16:09:40 14.932 

1/31/2013 16:09:50 11.918 

1/31/2013 16:10:00 11.352 

1/31/2013 16:10:10 11.286 

1/31/2013 16:10:201 11.271 

1/31/2013 16:10:30 11.271 

1/31/2013 16:10:40 10.511 

1/31/2013 16:10:50 9.492 

1/31/2013 16:11:00 9.415 

1/31/2013 16 :11:10 '"1-9::4';;04~' 

1/31/2013 16:11:20 9.064 

1/31/2013 16:11:30 7.701 

1/31/2013 16:11:40 7.542 

1/31/2013 16:11:50 7.526 

1/31/2013 16:12:oo"I-7:;;.~50::;8~ 

1/31/2013 16:12:10 6.581 

1/31/2013 16:12:20 4.104 

1/31/2013 16:12:30 3.856 

1/ 31/2013 16:12:40 3.818 

1/31/2013 16:12 :50'"1-3=-.=-81"'6"'" 

1/31/2013 16:13:00 4.734 

CO, 

% 

9.799 

5.83 

5.198 

7.668 

9.672 

5.492 

5.127 

5.141 

5.142 

5.143 

5.141 

5.14 

5.14 

5.141 

5.141 

5.14 

5.138 

5.136 

5.134 

5.133 

5.133 

5.132 

5.13 

5.133 

5.131 

5.13 

5.129 

5.128 

5.13 

S.127 

5.129 

5.13 

5.129 

5.129 

5.129 

5.129 

5.127 

5.127 

5.125 

5.128 

5.13 

5.127 

5.126 

5.127 

5.127 

5.126 

5.127 

5.126 

5.125 

5.126 

5.125 

5.126 

5.125 

5.125 

5.126 

5.125 

5.126 

5.123 

5.125 

NO" CO O2 NO. CO THe 

PPM PPM % PPM PPM PPM 

L...4,;;.~75;;7,..........,;9,;;.3;;;5;;.3 _...,1:;;8;;,.7.;,73:;-_4;;8;:,. 2;;5;,:1..J1 233.516 7.538 

3.593 9.371 ,....;1;,;2".8;,;4,;;7_-:3;;:6-:.0;,:1",8., 219.429 5.684 

L..",2~5;;39;-1-;;6.,"0:::16;-1-9~.",96~9:-......,;2~4;.;;.5~82,:-, 137.502 4.476 

2.518 4.393 9.965 24.467 134.064 3.632 

2.443 4.401 9.926 24.449 134.045 3.633 

0.776 4.377 9.915 7.362 97.849 3.631 

0.385 4.367 9.915 0.533 163.969 3.634 

0.309 4.348 9.911 0.45 235.579 3.637 

0.285 4.31 9.896 0.403 1 239.936 1 3.637 

0.245 4.298 9.891 0.38 192.939 3.635 

0.245 4.28 9.893 0.365 137.693 1 3.632 

0.226 4.266 9.9 

0.2 4.252 9.912 

0.189 4.22 9.915 

0.192 4.207 9.915 

0.182 4.191 9.915 

0.167 4.167 9.915 

0.154 4.152 9.914 

0.161 4.142 9.915 

0.15 4.147 9.916 

0.153 4.134 9.915 

0.143 4.136 9.914 

0.14 4.125 9.915 

0.144 4.133 9.915 

0.14 4.1 9.915 

0.141 4.124 9.915 

0.156 4.142 9.915 

0.169 4.123 9.915 

0.154 4.088 9.916 

0.158 4.086 9.915 

0.148 4.093 9.915 

0.143 4.107 9.916 

0.143 4.08 9.915 

0.162 4.06 9.915 

0.166 4.079 9.914 

0.164 4.092 9.915 

0.161 4.113 9.915 

0.15 4.106 9.914 

0.15 4.082 9.915 

0.145 4.079 9.915 

0.16 4.089 9.915 

0.155 4.057 9.915 

0.145 4.062 9.915 

0.151 4.08 9.915 

0.16 4.094 9.915 

0.156 4.062 9.915 

0.158 4.067 9.914 

0.163 4.073 9.915 

0.158 4.02 9.916 

0.158 4.022 9.916 

0.158 4.05 9.915 

0.147 4.047 9.916 

0.141 4.042 9.916 

0.143 4.073 9.923 

0.136 4.032 9.936 

0.133 4.014 9.941 

0.132 4.017 9.94 

0.144 4.011 9.94 

0.141 4.021 9.94 

0.341 

0.33 

0.323 

0.301 

0.29 

0.281 

0.266 

0.261 

0.26 

0.26 

0.261 

0.257 

0.25 

0.253 

0.258 

0.251 

0.256 

0.248 

0.249 

0.269 

0.256 

0.258 

0.288 

0.25 

0.24 

0.231 

0.234 

0.229 

0.231 

0.244 

0.244 

0.23 

0.23 

0.238 

0.245 

0.244 

0.231 

0.234 

0.245 

0.23 

0.23 

0.23 

0.23 

0.24 

0.241 

0.23 

0.229 

0.23 

117.183 

28.931 

5.257 

1.171 

0.453 

0.272 

0.24 

0.239 

0.236 

0.236 

0.242 

0.241 

0.237 

0.238 

0.236 

0.235 

0.235 

0.237 

0.237 

0.235 

0.237 

0.238 

0.241 

0.126 

0.205 

0.246 

0.129 

0.208 

0.123 

0.086 

0.204 

0.123 

0.202 

0.24 

0.124 

0.089 

0.084 

0.084 

0.199 

0.239 

0.244 

0.121 

0.208 

0.244 

0.243 

0.239 

0.242 

0.246 

3.631 

3.628 

3.626 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.626 

3.626 

3.627 

3.627 

3.627 

3.627 

3.627 

3.627 

3.626 

3.626 

3.627 

3.626 

3.626 

3.627 

3.626 

3.626 

3.626 

3.626 

3.627 

3.627 

3.628 

3.627 

3.627 

3.628 

3.628 

3.628 

3.629 

3.627 

3.628 

3.628 

3.628 

3.628 

3.627 

3.628 

Cal High 

Mid 

CO Mid 

C02 Cal High 

C02 Mid 

CO Cal High 

CO Mid 

80% 

80% 

60% 

50% 

40% 

20% 
0, 

Date Time % 

1/31/2013 16:13:10 9.487 

1/31/2013 16:13:20 10.083 

1/31/2013 16:13:30 10.158 

1/ 31/2013 16:13:40 10.18 

1/ 31/ 2013 16 13 501"'1-:1;:':0"i1~85~ 

1/ 31/ 2013 16:14:00 10.176 

1/ 31/ 2013 16:14

:10 13.406 

1/ 31/ 2013 16:14:20 15

.044 

1/31/2013 16:14:30 15.103 

1/31/2013 16:14:40 15.049 

1/31/2013 16:14:50 15.049 

1/ 31/2013 16:15:00 15.057 

1/ 31/ 2013 16:15:101 15

.058 

1/ 31/ 2013 16:15:20 13.864 

1/31/ 2013 16:15:30 11.474 

1/ 31/ 2013 16:15:40 11.258 

1/ 31/2013 16:15:50 11

.223 

1/31/2013 16:16:001 11.214 

1/31/2013 16:16:10 10.687 

1/31/2013 16:16:20 9.486 

1/ 31/2013 16:16:30 9.365 

1/ 31/ 2013 16:16:40

L

I ~93;:.4~ 

1/ 31/ 2013 16:16:50 8.256 

1/ 31/ 2013 16:17

:00 5.885 

1/ 31/2013 16:17:10 5.67 

1/31/2013 16:17:20 6.135 

1/31/2013 16:17:30 7.342 

1/31/2013 16:17:401 7.451 

1/ 31/2013 16:17:50 6.455 

1/ 31/ 2013 16:18:00 4.056 

1/ 31/ 2013 16:18:10 3.827 

1/ 31/2013 16:18:20 

3.797 

1/31/2013 16:18:301 3.794 

1/31/2013 16:18:40 4.973 

1/31/2013 16:18:50 9.5 

1/31/2013 16:19:00 9.998 

1/31/2013 16:19:10 10.067 

1/ 31/ 2013 16:19:201 10.085 

1/ 31/ 2013 16:19:30 10.079 

1/31/2013 16:19:40 12.527 

1/ 31/ 2013 16:19:50 14.883 

1/31/2013 16:20:00 15.026 

1/31/2013 16:20:10 15.052 

1/31/2013 16:20:20 15.061 

1/31/2013 16:20:30 15.06 

1/ 31/ 2013 16:20

:401 15.062 

1/ 31/ 2013 16:20:50 14.905 

1/ 31/ 2013 16:21

:00 11.92 

1/ 31/ 2013 16:21:10 11.308 

1/ 31/2013 16:21:20 11.236 

1/31/2013 16:21:301 11.224 

1/31/2013 16:21:40 10.698 

1/31/2013 16:21:50 9.504 

1/ 31/ 2013 16:22:00 9.372 

1/ 31/ 2013 16:22

:10 9.36 

1/ 31/ 2013 16:22:20 9.352 

1/ 31/ 2013 16:22:30 9.342 

1/ 31/2013 16:22:40 9.34 

1/31/2013 16:22:501"'1 """'9.';;33';9"'" 

CO, 

% 

5.123 5.126 5.122 5.121 5.123 5.123 5.122 5.122 

5.121 

5.12 

5.119 

5.12 5.12 5.12 5.119 5.118 

5.117 

5.117 

5.115 

5.115 5.116 5.115 

5.114 

5.114 

5.112 5.113 

5.115 5.112 5.11 5.112 5.111 5.111 

5.11 5.109 

5.107 

5.108 5.107 

5.108 5.107 

5.112 

5.109 

5.107 

5.106 

5.106 

5.105 

5.104 5.103 5.104 

5.103 

5.103 

5.105 5.104 5.104 5.102 5.103 5.102 5.1 5.1 

5.101 

NO, 

PPM 

0.137 0.132 0.125 0.127 0.126 0.124 0.13 0.13 0.124 0.122 0.12 0.117 0.119 0.116 0.117 0.119 0.111 0.115 

0.114 0.115 0.117 0.145 0.142 0.118 0.109 

0.105 0.108 

0.107 0.108 0.109 0.1 0.105 0.1 

0.091 0.091 

0.092 0.093 0.105 0.105 0.095 0.094 0.097 0.096 0.09 0.097 0.085 0.085 0.094 0.089 0.086 

0.084 

0.086 0.096 0.101 0.092 0.09 

0.093 0.093 

0.088 

co 

PPM 4.01 

4.019 4.033 4.01 4.013 4.02 3.989 3.983 

3.987 

3.996 4.016 

3.999 4.014 4.008 3.984 3.963 

3.987 

3.981 

3.976 

3.96 

3.979 3.987 3.975 3.965 

3.953 3.963 

3.969 3.979 3.965 3.941 3.949 3.941 3.892 3.941 

3.931 3.927 3.926 3.92 3.907 3.901 3.891 3.904 

3.918 

3.907 

3.87 

3.892 3.917 3.873 3.871 

3.871 

3.883 

3.889 

3.889 

3.9 

3.888 

3.876 

3.854 

3.851 

3.859 

0, 

% 

9.94 9.939 

9.941 9.94 9.939 9.94 9.94 9.94 

9.94 

9.939 9.94 9.94 9.94 9.939 9.94 9.94 9.94 

9.939 9.939 9.939 9.94 9.94 9.938 9.94 

9.94 9.94 9.939 9.939 9.94 9.939 9.94 9.939 9.939 

9.939 9.941 

9.939 9.94 9.941 9.942 9.947 9.963 

9.964 

9.964 

9.963 

9.961 

9.965 9.964 9.964 

9.965 

9.965 

9.966 

9.965 

9.965 9.965 9.965 9.965 9.965 9.965 9.965 

NO, 

PPM 

0.228 

0.227 0.238 0.219 0.218 0.224 0.216 0.218 0.215 

0.224 0.221 0.223 0.215 0.215 0.215 

0.226 0.215 0.214 0.22 0.219 0.221 0.214 0.211 

0.199 0.214 

0.201 0.206 0.208 0.203 0.199 0.2 0.228 0.2 0.199 0.199 0.202 0.199 0.206 0.199 0.199 0.199 0.199 

0.2 

0.196 

0.199 

0.207 

0.206 

0.199 

0.199 

0.197 

0.2 

0.199 

0.199 

0.189 

0.184 

0.196 

0. 188 0.189 

0.199 

co 

PPM 

0.246 

0.242 

0.244 0.245 0.239 0.237 0.239 0.239 

0.234 

0.24 0.24 

0.24 0.235 0.239 0.242 0.24 0.24 

0.239 

0.24 

0.114 0.203 0.239 0.237 0.237 0.236 

0.237 

0.235 

0.119 0.205 0.24 0.238 0.239 0.237 

0.24 

0.239 

0.237 

0.235 

0.236 

0.243 

0.238 

0.243 

0.244 

0.241 

0.242 

0.117 

0.209 0.242 

0.241 

0.125 

0.207 

0.242 

0.242 0.119 0.208 0.241 0.243 

0.243 

0.238 

0.238 

THe 

PPM 

3.629 

3.627 

3.627 3.628 3.628 3.627 3.628 3.627 

3.628 

3.628 

3.628 3.628 3.629 3.629 3.629 

3.63 

3.629 

3.629 

3.628 3.629 3.628 3.628 3.629 

3.629 3.629 

3.629 3.629 3.628 3.628 3.628 3.627 

3.628 3.628 

3.628 3.628 3.628 3.628 3.627 3.628 3.628 3.627 3.628 3.628 3.627 3.628 3.627 3.627 3.628 3.627 3.627 3.627 3.627 3.628 3.627 3.628 3.628 3.627 3.628 

3.628 

Mid M id 

80% 

60% 50% 

40% 

20% 

80% 

60% 

50% 
0, 

Date Time % 

1/31/2013 16:23:00 9.341 

1/31/2013 16:23:10 9.339 

1/31/2013 16:23:20 9.338 

1/31/2013 16:23:301"1 ~9i:-;'33;:'9~ 

1/31/2013 16:23:40 9.098 

1/31/2013 16:23:50 4.79 

1/31/2013 16:24:00 3.91 

1/31/2013 16:24:10 3.819 

1/31/2013 16:24:20 3.795 

1/31/2013 16:24:301"1 -3~.;;:79~4"" 

1/31/2013 16:24:40 3.793 

1/31/2013 16:24:50 5.685 

1/31/2013 16:25:00 9.661 

1/31/2013 16:25:10 10.024 

1/31/2013 16:25:20 10.064 

1/31/2013 16:25:30 8.694 

1/31/2013 16:25:40 7.58 

1/31/2013 16:25:50 7.501 

1/31/2013 16:26:00 7.48 

1/31/2013 16:26:101"1-7:;".4':'7;';:9~ 

1/31/2013 16:26:20 7.736 

1/31/2013 16:26:30 9.771 

1/31/2013 16:26:40 10.065 

1/31/2013 16:26:50 10.106 

1/31/2013 16:27:001 10.109 

1/31/2013 16:27:10 10.093 

1/31/2013 16:27:20 12.663 

1/31/2013 16:27:30 14.89 

1/31/2013 16:27:40 15.031 

1/31/2013 16:27:50 15.053 

1/31/2013 16:28:001 15.062 

1/31/2013 16:28:10 14.015 

1/31/2013 16:28:20 11.514 

1/31/2013 16:28:30 11.273 

1/31/2013 16:28:40 11.233 

1/31/2013 16:28:50 11.223 

1/31/2013 16:29:00 11.222 

1/31/2013 16:29:101 11.221 

1/31/2013 16:29:20 10.744 

1/31/2013 16:29:30 9.526 

1/31/2013 16:29:40 9.372 

1/31/2013 16:29:50 9.363 

1/31/2013 16:30:001"1 ~9i:-.'::35"i8~ 

1/31/2013 16:30:10 8.794 

1/31/2013 16:30:20 7.61 

1/31/2013 16:30:30 7.503 

1/31/2013 16:30 401....,7'='4':'7:::9~ 

1/31/2013 16:30:50 7.479 

1/31/2013 16:31:00 6.902 

1/31/2013 16:31:10 4.188 

1/31/2013 16:31:20 3.846 

1/31/2013 16:31:30 3.803 

1/31/2013 16:31:401 3.794 

1/31/2013 16:31:50 5.848 

1/31/2013 16:32:00 9.7 

1/31/2013 16:32:10 10.038 

1/31/2013 16:32:20 10.088 

1/31/2013 16:32:30 10.109 

1/31/2013 16:32:40 10.109 

CO, 

% 

5.101 

5.1 

5.101 

5.098 

5.099 

5.101 

5.101 

5.099 

5.098 

5.096 

5.098 

5.095 

5.096 

5.096 

5.094 

5.095 

5.096 

5.096 

5.094 

5.093 

5.095 

5.093 

5.094 

5.09 5.089 

5.09 

5.09 

5.092 

5.09 

5.087 

5.088 

5.089 

5.088 

5.087 

5.087 

5.087 

5.085 

5.085 

5.085 

5.086 

5.083 

5.084 

5.083 

5.083 

5.083 

5.08 5.08 

5.08 

5.08 

5.079 

5.079 5.081 

5.079 5.077 

5.079 

5.Q78 5.078 

5.076 

5.079 

NO, 

PPM 0.082 

0.082 0.085 

0.088 0.085 

0.Q78 0.077 

0.09 0.095 

0.081 

0.081 

0.Q78 

0.078 0.081 0.081 0.079 

0.082 

0.079 

0.074 

0.075 

0.074 0.07 0.067 

0.067 0.072 

0.082 

0.073 

0.073 

0.071 

0.07 0.064 0.071 

0.079 

0.07 

0.069 

0.065 

0.066 

0.077 0.071 

0.07 

0.067 

0.066 

0.068 

0.062 

0.058 0.065 0.063 0.071 

0.067 

0.085 

0.083 

0.069 

0.061 

0.064 0.071 

0.069 

0.074 

0.079 

0.085 

co 

PPM 

3.881 

3.884 

3.872 

3.866 

3.855 

3.849 

3.841 

3.851 

3.847 

3.859 

3.833 

3.847 

3.842 3.815 

3.806 3.8 

3.808 

3.822 

3.836 

3.82 

3.801 

3.814 

3.803 

3.796 

3.766 

3.788 

3.809 3.779 3.795 3.764 3.772 

3.774 

3.778 

3.799 

3.788 

3.768 3.75 

3.748 3.754 

3.731 

3.75 

3.741 

3.726 

3.745 

3.751 

3.766 

3.725 

3.715 

3.724 

3.74 

3.722 

3.738 

3.751 

3.737 3.712 3.699 

3.697 

3.723 

3.715 

0, 

% 

9.966 

9.966 

9.964 

9.965 

9.965 

9.965 

9.966 

9.965 

9.964 

9.964 

9.965 

9.965 

9.965 

9.965 

9.965 

9.966 

9.972 

9.982 

9.988 

9.989 

9.987 

9.988 

9.99 

9.986 

9.987 

9.986 

9.982 

9.988 

9.988 

9.986 

9.988 

9.99 

9.991 

9.99 

9.989 

9.991 

9.99 

9.99 

9.991 9.99 

9.99 

9.99 

9.992 

9.99 

9.989 

9.989 

9.99 

9.989 

9.989 9.99 

9.99 

9.988 

9.99 

9.99 

9.989 9.989 

9.99 

9.99 

9.989 

NO, 

PPM 

0.194 

0.184 

0.196 0.203 0.185 

0.194 

0.19 0.184 

0.184 

0.185 

0.185 

0.198 

0.186 0.197 0.184 

0.186 

0.185 

0.19 

0.187 

0.184 

0.184 

0.184 

0.184 

0.184 

0.185 

0.191 

0.184 

0.184 

0.185 

0.184 0.184 0.185 

0.184 

0.189 

0.193 

0.169 

0.19 

0.187 

0.181 0.169 

0.169 

0.169 

0.176 

0.177 

0.184 0.194 0.183 

0.169 

0.17 

0.173 

0.184 

0.177 

0.169 0.172 0.169 0.169 0.169 0.162 

0.169 

co 

PPM 

0.237 

0.241 

0.238 

0.238 

0.236 

0.235 

0.242 

0.239 

0.119 

0.198 

0.241 

0.235 

0.239 

0.234 0.234 

0.236 

0.237 

0.235 

0.121 

0.083 

0.199 

0.232 

0.235 

0.234 

0.229 

0.115 

0.196 

0.234 

0.237 

0.237 

0.24 

0.235 

0.237 

0.232 

0.231 

0.236 

0.112 

0.201 

0.123 

0.086 

0.204 

0.237 

0.244 

0.243 

0.232 

0.235 

0.239 

0.236 

0.118 

0.085 

0.195 

0.12 

0.2 

0.231 

0.233 0.233 

0.112 

0.199 

0.238 

THe 

PPM 

3.628 

3.627 

3.628 3.628 

3.627 3.628 

3.626 

3.628 

3.628 

3.628 

3.627 

3.627 3.627 3.627 3.628 

3.628 

3.628 

3.628 

3.628 3.627 

3.628 3.627 

3.628 

3.627 

3.628 

3.628 

3.629 3.628 

3.628 3.629 3.628 

3.629 

3.628 

3.628 

3.629 

3.628 3.629 

3.628 3.628 3.628 

3.628 

3.629 

3.628 

3.628 3.629 3.628 3.628 

3.629 

3.629 

3.628 

3.629 

3.629 3.628 3.628 3.628 3.629 3.628 3.628 

3.627 

Mid 

40% 

20% 

40% 

80% 

60% 

50% 

40% 

20% 
0, CO, NO, CO 0, NO, CO THe 

Date Time % % PPM PPM % PPM PPM PPM 

1/31/2013 16:32:50 10.111 5.077 0.109 3.692 9.99 0.169 0.119 3.627 

1/31/2013 16:33:00 10.11 5.075 0.12 3.695 9.99 0.169 0.082 3.627 

1/31/2013 16:33:101 10.111 5.076 0.131 3.683 9.99 0.169 0.2 3.627 Mid 

1/31/2013 16:33:20 10.111 5.074 0.142 3.659 9.99 0.169 0.237 3.628 

1/31/2013 16:34:00 10.111 5.07 0.183 3.671 10.003 0.172 0.237 3.628 

1/31/2013 16:35:00 10.11 5.07 0.208 3.66 10.007 0.167 0.121 3.628 
~ ~ N~ W ~ ~ W ~C 

Date Time % % PPM PPM % PPM PPM PPM 

2/1/2013 7:51:00 0.105 -0.1041 -0.0251 -0.023 0.0331 0.0531 -0.161 2.049 N2/NOx Mode 

2/1/2013 7:52:00 0.104 -0.006 -0.022 -0.03 0.032...---::,;0',::;05:;, -0.164 1.942 

2/1/2013 7:53:00 0.103 -0.011 -0.032 -0.026 0.032 0.045 -0.166 2.625 N2/NO Mode 

2/1/2013 7:54:00 0.103 -0.015 2.935L..._-..::0:.;.0::;2:;.8_.,.;::0.::;0;:3201 2.89 -0.135 0.001 Cal Zero 

2/1/2013 7:55:00 15.519 7.796 4.819 4.397 12.748 4.881 37.46 -0.009 

2/1/2013 7:56:00 ...-...;1:;;:9..::.1:;;:17;,...._:;.9.'"'64,:.:3+-......;4;;:.8,,1:.:;2 ..... --:.::,9.:;;:3:;.8 _..::1;8.:;;:9;:55+-_,:4:;;.8;;:8 ..... 2;;;3:;;:0,;;. 7~3;;!1 f-_-;O.:;;:OO;;;l;JNO/NOX Mode;THC Zero 

2/1/2013 7:57:00 19.142 9.661 4.814 9.447 18.965 4.885 242.805 7.574 Cal High 

2/1/2013 7:58:00 11869 5889 4816 9455 12757 4886 238903 77.933 

2/1/2013 7:59:00 79.903 NO/NO Mode 

2/1/2013 8:00:00 80.087 Mid 

2/1/2013 8:01:00 80.633 N02/NO Mode 

2/1/2013 8:02:00 10.17 5.048 1.637 4.458 10.048 1.788 139.192 81.297 

2/1/2013 8:03:00 10.168 5.046r

l-"::3'::.8:;:4';'81 4.474 10.0481 3.9221 139.31 81.638 N02/NOx Mode 

2/1/2013 8:04:00 13.493 4.187 2.023 3.399 2.486 2.227 82.898 81.741 

2/1/2013 8:05:00 14.051 3.988 -0.013 4.144 0.048 0.064 0.449 81.79 

2/1/2013 8:06:00 14.071 3.9691 -0.0181 2.449 0.0271 0.0581 -0.051 83.499 NOx Cal Zero 

2/1/2013 8:07:00 14.042 3.984 3.935 2.84 0.027 36.418 0.024 85.38 

2/1/2013 8:08:00 14.098 3.945 4.793 2.872 0.027 48.845 0.051"1-"::8=-5.:::84;ITHC High 

2/1/2013 8:09:00 14.054 3.968rl--=4"::.7:::8;71 2.195 0.3081 48.7751 1.275 72.822 NOx Cal High 

2/1/2013 8:10:00 14.069 3.955 3.294 3.373 0.026 22.754 0.07 47.253 

2/1/2013 8:11:00 14.05 3.967 2.557 2.391 0.027 23.365 -0.002 47.124 

2/1/2013 8:12:00 12.866 3.7441r -':;2:';.5:;:4';'11 2.391 0.1561 24.4531 0.448 47.267 Mid 

2/1/2013 8:13:00 0.345 0.019 0.597 3.99 0.038 5.841 101.418 47.534 

2/1/2013 8:14:00 0.127 0.008 -0.023 1-....;::4 .. ..::,45:;,1 0.025 0.198rl-1~3:.;9;.;.0:.;5:;.6--=4;;7.:::64::;3Iw bias;THC Mid 

2/1/2013 8:15:00 1.219 0.672 -0.025 4.351 2.939 0.162 130.631 39.07 

2/1/2013 8:16:00 ...-~9..::.9:::68:::...._;:5.;05:;.:3:...........,-,.::0:;;.0:;,2 0.675 9.887 0.183 15.598 

2/1/2013 8:17:00 I 10.041 5.079 -0.0271 -0.337:rl-..::9..::.9::;.05:,..........:0:;;.2:::0:;;,81 -0.4121 

2/1/2013 8:18:00 L......::::6;.::.5:::13:::....-=-3 . .::.20;,;2:.....-.:0:::.8::1;:,J6 -0.322 5.299 10.234 -0.382 

2/1/2013 8:19:00 0.143 0.039 2.525 0.025 0.043 24.567 -0.137 

2/1/2013 8:20:00 "I -..::0..::.1;23;;....-.::,0::..0:;.:3:.....-.::::2:;.5:;;:3-...::0..::.1::;2;.2 --.::.0.::,0;:.26;,....-.::.24;;;.5:;;8:;5---..::0..::.0:;:5"'71 

2/1/2013 8:21:00 0.123 0.031 2.529 0.123 0.026 24.584 -0.107 

2/1/2013 8:22:00 0.122 0.031 2.523 0.119 0.025 24.601 -0.06 

2/1/2013 8:23:00 0.122 0.034 2.523 0.115 0.025 24.58 -0.132 

2/1/2013 8:24:00 10.08 3.3 2.763 1.224 10.485 25.265 71.95 

2/1/2013 8:25:00 13.431 4.306 3.283 1.292 13.222 28.304 85.17 

2/1/2013 8:26:00 13.474 4.292 2.787 2.09 13.27 26.811 137.763 

2/1/2013 8:27:00 13.496 4.287 3.211 1.15 13.244 28.41 74.438 

2/1/2013 8:28:00 13.478 4.304 2.936 1.831 13.268 27.684 122.314 

2/1/2013 8:29:00 13.427 4.339 3.211 1.013 13.248 28.526 66.829 

2/1/2013 8:30:00 13.422 4.346 2.937 1.638 13.264 28.2 112.971 

2/1/2013 8:31:00 13.363 4.385 3.153 1.03 13.242 28.685 66.48 

2/1/2013 8:32:00 13.377 4.38 3.072 1.272 13.251 28.835 81.47 

2/1/2013 8:33:00 13.307 4.421 3.331 0.783 13.192 29.742 52.914 

2/1/2013 8:34:00 13.333 4.412 3.022 0.88 13.227 29.277 58.348 

2/1/2013 8:35:00 13.319 4.425 3.2 0.884 13.193 29.392 60.798 

2/1/2013 8:36:00 8.145 2.676 3.555 0.742 13.195 29.574 55.742 

2/1/2013 8:37:00 0.187 0.119 4.739 0.225 13.191 29.597 54.919 

2/1/2013 8:38:00 rl-..,0:::.1:::6"'6--.::.0.:;:1;:12;,....-4;:..7;,;3"'9:..........;0:::.1:;;:5::;,71 13.195 29.74 53.301 

2/1/2013 8:39:00 4.59 1.611 4.204 0.202 13.194 29.599 53.643 

2/1/2013 8:40:00 13.268 4.428 3.021 0.676 13.197 29.588 54.524 

2/1/2013 8:41:00 13.298 4.445 3.075 0.809 13.195 29.673 53.681 

2/1/2013 8.42:00 13.307 4.45 3.073 0.776 13.197 29.615 53.796 

2/1/2013 8:43:00 13.319 4.452 3.001 0.805 13.205 29.573 53.324 

2/1/2013 8:44:00 13.314 4.459 3.026 0.805 13.195 29.623 53.162 

2/1/2013 8:45:00 13.329 4.458 2.964 0.831 13.213 29.652 53.217 

2/1/2013 8:46:00 13.336 4.457 2.986 0.745 13.227 29.698 50.782 

2/1/2013 8:47:00 13.343 4.459 2.963 0.78 13.23 29.521 52.825 

25.89 

25.747102/c02 bias;THC Low 

24.629 

0.704 

·0.017 NOx bias 

-0.017 

-0.018 

-0.017 

19.967 

15.512 

35.268 

10.37 

30.106 

8.296 

27.77 

10.075 

15.203 

6.624 

8.045 

8.676 

7.172 

7.154 

6.772 NOx bias 

6.936 

7.013 

6.896 

6.975 

6.842 

6.572 

6.988 

6.229 

6.71 
Date Time 

2/1/2013 8:48:00 

2/1/ 2013 8:49:00 

2/1/2013 8:50:00 

2/1/2013 8:51:00 

2/1/2013 8:52:00 

2/1/2013 8:53:00 

2/1/2013 8:54:00 

2/1/2013 8:55:00 

2/1/2013 8:56:00 

2/1/2013 8:57:00 

2/1/2013 8:58:00 

2/1/2013 8:59:00 

2/ 1/2013 9:00:00 

2/1/2013 9:01:00 

2/1/2013 9:02:00 

2/1/2013 9:03:00 

2/1/2013 9:04:00 

2/ 1/ 2013 9:05:00 

2/ 1/2013 9:06:00 

2/1/2013 9:07:00 

2/1/2013 9:08:00 

2/1/2013 9:09:00 

2/1/2013 9:10:00 

2/1/ 2013 9:11:00 

2/1/2013 9:12:00 

2/1/2013 9:13:00 

2/1/2013 9:14:00 

2/1/2013 9:15:00 

2/1/2013 9:16:00 

2/ 1/2013 9:17:00 

2/1/2013 9:18:00 

2/1/2013 9:19:00 

2/1/2013 9:20:00 

2/1/2013 9:21:00 

2/ 1/ 2013 9:22:00 

2/1/2013 9:23:00 

2/1/2013 9:24:00 

2/1/2013 9:25:00 

2/1/2013 9:26:00 

2/1/ 2013 9:27:00 

2/1/ 2013 9:28:00 

2/1/2013 9:29:00 

2/1/2013 9:30:00 

2/1/2013 9:31:00 

2/1/2013 9:32:00 

2/1/ 2013 9:33:00 

2/1/2013 9:34:00 

2/1/2013 9:35:00 

2/1/2013 9:36:00 

2/1/2013 9:37:00 

2/1/ 2013 9:38:00 

2/ 1/ 2013 9:39:00 

2/1/2013 9:40:00 

2/1/2013 9:41:00 

2/1/2013 9:42:00 

2/1/2013 9:43:00 

2/ 1/2013 9:44:00 

2/1/ 2013 9:45:00 

2/1/2013 9:46:00 

0, 

% 

13.344 

13.349 

13.353 

13.366 

13.366 

13.37 

13.37 

13.372 

13.38 

13.39 

13.4 

13.404 

13.403 

13.411 

13.418 

13.413 

13.413 

13.425 

13.429 

13.432 

13.437 

13.43 

13.432 

13.438 

13.45 

13.437 

13.445 

13.45 

13.476 

13.486 

13.492 

13.493 

13.494 

13.482 

13.483 

13.478 

13.468 

13.471 

16.005 

14.316 

13.626 

13.624 

13.627 

13.64 

13.63 

13.521 

13.492 

13.497 

13.467 

13.436 

13.427 

13.43 

13.43 

13.427 

13.428 

17.212 

14.721 

13.463 

13.473 

CO2 NO~ CO 

% PPM PPM 

4.463 2.947 0.792 

4.466 3.025 0.72 

4.467 2.965 0.699 

4.466 2.895 0.733 

4.469 2.98 0.735 

4.47 2.977 0.752 

4.473 2.931 0.76 

4.476 2.983 0.737 

4.472 2.903 0.742 

4.466 2.882 0.731 

4.463 2.863 0.734 

4.462 2.77 0.742 

4.463 2.762 0.783 

4.462 2.939 0.784 

4.458 2.978 0.713 

4.461 2.921 0.739 

4.464 2.882 0.733 

4.456 2.785 0.732 

4.454 2.76 0.755 

4.448 2.858 0.781 

4.448 2.845 0.735 

4.452 2.838 0.739 

4.453 2.831 0.748 

4.451 2.847 0.765 

4.449 2.84 0.773 

4.455 2.888 0.73 

4.453 2.772 0.713 

4.453 2.685 0.706 

4.445 2.716 0.718 

4.443 2.825 0.763 

4.441 2.854 0.752 

4.444 2.911 0.759 

4.445 2.886 0.746 

4.451 2.888 0.746 

4.454 2.924 0.683 

4.457 2.885 0.636 

4.461 2.813 0.631 

4.461 2.816 0.64 

3.015 1.919 0.538 

3.944 2.525 0.429 

4.359 2.788 0.601 

4.357 2.931 0.605 

4.356 2.844 0.615 

4.348 2.71 0.627 

4.351 2.788 0.627 

4.419 2.781 0.645 

4.436 2.83 0.677 

4.432 2.815 0.631 

4.449 2.875 0.631 

4.462 2.883 0.642 

4.472 2.954 0.632 

4.471 2.914 0.621 

4.468 2.866 0.622 

4.471 2.838 0.623 

4.471 2.777 0.653 

2.314 1.441 0.527 

3.69 2.313 0.308 

4.449 2.886 0.488 

4.446 2.941 0.507 

13.236 29.638 

13.237 29.851 

13.247 29.79 

13.239 29.653 

13.244 29.85 

13.25 29.762 

13.244 29.812 

13.247 29.961 

13.259 29.913 

13.271 29.931 

13.278 29.869 

13.288 29.781 

13.283 29.747 

13.294 29.918 

13.295 29.924 

13.288 29.997 

13.289 30.097 

13.299 30.091 

13.315 29.915 

13.317 29.981 

13.309 30.102 

13.319 30.036 

13.319 29.968 

13.324 29.999 

13.329 30.002 

13.318 30.25 

13.336 30.237 

13.334 30.261 

13.339 30.113 

13.343 29.994 

13.344 29.966 

13.345 30.064 

13.346 30.035 

13.346 29.968 

13.346 30.3 

13.346 30.245 

13.343 30.278 

13.345 30.385 

13.345 30.47 

13.345 30.342 

13.344 30.466 

13.345 30.584 

13.345 30.37 

13.342 30.393 

13.341 30.379 

13.344 30.225 

13.344 30.216 

13.344 30.28 

13.345 30.347 

13.342 30.353 

13.339 30.5 

13.346 30.396 

13.342 30.462 

13.343 30.297 

13.344 30.268 

13.345 30.252 

13.344 30.471 

13.335 30.455 

13.344 30.472 

co 

PPM 

52.007 

48.702 

49.834 

51.932 

50.714 

52.302 

51.585 

51.182 

51.242 

50.373 

50.927 

51.431 

53.761 

51.624 

49.46 

51.265 

50.552 

50.409 

51.275 

51.813 

51.435 

51.386 

51.429 

51.869 

52.164 

49.41 

49.472 

48.573 

49.668 

52.707 

50.984 

50.475 

50.274 

51.089 

49.837 

48.105 

48.08 

47.915 

46.054 

47.234 

46.102 

45.441 

47.557 

46.574 

47.29 

48.08 

48.66 

47.917 

47.854 

47.533 

48.207 

47.962 

46.927 

48.268 

49.052 

49.322 

47.902 

47.93 

46.5 

THe 

PPM 

6.581 

5.662 

5.9 

6.477 

6.368 

6.863 

6.53 

6.536 

6.395 

6.249 

6.195 

6.276 

6.656 

6.526 

5.978 

6.431 

6.283 

6.296 

6.427 

6.542 

6.603 

6.227 

6.221 

6.504 

6.678 

6.1 

5.687 

5.83 

6.007 

6.804 

6.293 

6.219 

6.063 

6.246 

6.137 

5.758 

5.675 

5.711 

5.262 

5.565 

5.278 

5.243 

5.895 

5.445 

5.566 

5.718 

5.738 

5.623 

5.741 

5.584 

5.823 

5.841 

5.505 

5.912 

6.06 

6.053 

5.805 

5.76 

5.431 
~ ~ ~ ro ~ ~ ro 

Date Time % % PPM PPM % PPM PPM 

2/1/2013 9:47:00 13.491 4.435 2.948 0.502 13.344 30.486 47.273 

2/1/2013 9:48:00 13.508 4.426 2.939 0.475 13.345 30.495 46.707 

2/1/2013 9:49:00 13.497 4.428 2.867 0.495 13.342 30.497 47.025 

2/ 1/2013 9:50:00 13.449 4.462 2.701 0.473 13.342 30.504 48.292 

2/ 1/ 2013 9:51:00 13.421 4.482 2.874 0.409 13.344 30.48 48.838 

2/ 1/ 2013 9:52:00 13.414 4.485 2.79 0.413 13.333 30.622 46.853 

2/ 1/ 2013 9:53:00 13.406 4.491 2.822 0.392 13.34 30.669 46.952 

2/ 1/2013 9:54:00 13.417 4.484 2.836 0.403 13.336 30.658 46.727 

2/1/2013 9:55:00 13.424 4.479 2.922 0.413 13.345 30.534 46.855 

2/1/2013 9:56:00 13.448 4.463 2.707 0.42 13.35 30.379 48.915 

2/1/2013 9:57:00 13.429 4.475 2.859 0.416 13.339 30.558 48.111 

2/ 1/2013 9:58:00 13.424 4.48 2.914 0.438 13.339 30.672 48.475 

2/ 1/ 2013 9:59:00 13.422 4.484 2.949 0.393 13.331 30.736 47.053 

2/ 1/ 2013 10:00:00 16.266 2.879 1.897 0.365 13.334 30.703 46.979 

2/ 1/ 2013 10:01:00 20.764 0.239 0.037 0.115 13.34 30.467 49.599 

2/ 1/ 2013 10:02:00 20.884 0.174 0.002 0.169 13.343 30.352 50.781 

2/ 1/2013 10:03:00 20.895 0.169 0.007 0.247 13.343 30.474 49.863 

2/1/2013 10:04:00 20.898 0.169 0.015 0.181 13.342 30.775 42.614 

2/1/2013 10:05:00 20.899 0.167 0.016 0.136 13.342 30.471 44.147 

2/ 1/2013 10:06:00 20.891 0.171 0.004 0.127 13.341 30.294 47.462 

2/ 1/ 2013 10:07:00 20.898 0.166 -0.002 0.122 13.328 30.633 46.049 

2/ 1/ 2013 10:08:00 20.898 0.167 0.012 0.113 13.334 30.677 42.664 

2/ 1/ 2013 10:09:00 20.898 0.166 0.008 0.109 13.326 30.34 49.571 

2/ 1/ 2013 10:10:00 20.898 0.171 -0.01 0.114 13.337 30.184 53.895 

2/ 1/ 2013 10:11:00 20.89 0.177 -0.003 0.12 13.34 30.187 52.19 

2/1/2013 10:12:00 20.902 0.17 0 0.122 13.337 30.503 43.978 

2/1/2013 10:13:00 20.911 0.168 -0.014 0.145 13.343 30.308 43.783 

2/1/2013 10:14:00 20.911 0.172 -0.014 0.148 13.343 30.075 49.362 

2/1/ 2013 10:15:00 20.906 0.174 -0.012 0.134 13.336 30.291 50.485 

2/ 1/2013 10:16:00 19.965 0.182 0.195 0.179 13.34 30.365 45.645 

2/1/ 2013 10:17:00 20.889 0.177 0.078 0.192 13.323 30.341 46.986 

2/ 1/ 2013 10:18:00 14.484 3.997 2.156 0.494 13.327 30.203 52.113 

2/ 1/2013 10:19:00 13.489 4.479 2.702 0.773 13.316 30.355 50.691 

2/1/2013 10:20:00 13.492 4.48 2.594 0.733 13.334 30.264 48.649 

2/1/2013 10:21:00 13.493 4.483 2.575 0.698 13.331 30.276 47.543 

2/1/2013 10:22:00 13.477 4.489 2.787 0.739 13.312 30.44 50.725 

2/1/2013 10:23:00 13.475 4.492 2.623 0.681 13.319 30.499 46.567 

2/ 1/ 2013 10:24:00 13.478 4.489 2.598 0.667 13.322 30.284 47.717 

2/ 1/ 2013 10:25:00 13.475 4.488 2.665 0.724 13.319 30.268 46.611 

2/ 1/2013 10:26:00 13.49 4.479 2.649 0.707 13.319 30.13 47.982 

2/ 1/ 2013 10:27:00 13.488 4.481 2.753 0.736 13.325 30.242 47.013 

2/ 1/2013 10:28:00 13.49 4.481 2.794 0.715 13.326 30.208 48.217 

2/1/2013 10:29:00 13.499 4.477 2.802 0.702 13.328 30.125 46.092 

2/1/2013 10:30:00 13.487 4.482 2.795 0.695 13.329 30.159 46.179 

2/ 1/ 2013 10:31:00 13.479 4.488 2.739 0.637 13.315 30.429 44.313 

2/ 1/ 2013 10:32:00 13.468 4.499 2.748 0.527 13.316 30.452 40.961 

2/ 1/ 2013 10:33:00 13.473 4.496 2.767 0.601 13.318 30.25 46.279 

2/ 1/ 2013 10:34:00 13.469 4.497 2.735 0.634 13.316 30.342 45.157 

2/1/ 2013 10:35:00 13.474 4.493 2.708 0.609 13.315 30.257 45.61 

2/1/ 2013 10:36:00 13.059 4.287 2.36 0.583 11.257 17.017 36.147 

2/1/2013 10:37:00 10.128 5.235 -0.006 -0.214 9.917 1.073 0.896 

2/1/2013 10: 38: 00 r, """;"7,1 o;;'.1:----;5"'. 2:::4~5 -~.o::':. 0;;;1~8' .0.367' r --:-:9.-:-:9;;,17;-----;0;';.9::-1':17' -0.47 

2/ 1/2013 10:39:00 10.573 5.133 0.228 -0.348 4.61 12.806 0.312 

2/ 1/ 2013 10:40:00 13.432 4.502 2.644 0.58 0.053 24.868 0.062 

2/ 1/ 2013 10:41:00 8.499 2.81 3.159 0.678 0.034 24.854 -0.151 

2/ 1/ 2013 10:42:00'", -"'0".2"2"'4 --:::-0=::18"'1:-.....;4~. :;1;;2-~0,:,:1:::7;;6 -....;,0 . ..;0"'25,;........:,,;;4;;;8"2.....;~0;;;1;;;1.;4' 

2/ 1/ 2013 10:43:00 0.195 0.168 4.405 0.244 0.Q28 14.601 20.95 

2/ 1/ 2013 10:44:00 0.175 0.164 0.006 3.631 0.023 0.596 132.836 

THC 

PPM 

5.77 

5.576 

5.484 

5.691 

6.084 

5.745 

5.654 

5.598 

5.524 

5.981 

5.799 

6.138 

5.65 

5.726 

6.501 

6.718 

6.539 

4.245 

4.453 

5.229 

5.022 

4.094 

5.877 

6.683 

6.096 

4. 264 

4.229 

5.447 

5.892 

4.917 

5.004 

6.014 

5.607 

5.441 

4.97 

6.144 

5.084 

5.544 

4.912 

5.068 

4.774 

5.269 

4.714 

5.027 

4.591 

3.793 

4.94 

4.879 

4.805 

3.768 

-0.009 

-0.019 02/C02 bias 

0.145 

-0.019 

-0.019 

·0.019 NOx bias 

-0.018 

-0.013 
~ ~ N~ W 0, N~ W 

Date Time % % PPM PPM % PPM PPM 

2/1/2013 10:45:00 0.17 0.161 -0.0261 ..... _4~.~43~1 0.023 0.5171 138.5811 

2/1/2013 10:46:00 8.98 4.763 3.621 4.44 7.55 16.578 135.155 

2/1/2013 10:47:00 10.064 5.255 4.759 4.446 9.968 24.502 138.205 

2/1/2013 10:48:001"1-:1;.;0:':.0:::6::'5 -~5.~2~58;--4:"'. 7;:5:-;;8.....,-:4~.4:':'5.,;.2 ---;:.9.'i:9~68;--.,;.24:"'.:=,51:-;8.....,,;,13;;8:':8;-;8~11 

2/1/2013 10:49:00 10.065 5.257 4.758 4.448 9.968 24.52 138.647 

2/1/2013 10:50:00 1.371 0.616 0.935 2.328 2.937 10.558 81.048 

2/1/2013 10:51:00 0.096 0.135 -0.028 0.004 0.024 0.155 0.423 

2/ 1/2013 10 52 :00 1"1-";0";0;;9~6---;:'0~1;:;34;--:-0.0;;;3;;:3---";0";.0;;:2';'3---;:'0.;;;0:';'24;--0~~12;;:7"""-;-0;;'2:;o"'81 

2/1/2013 10:53:00 0.156 0.157 -0.029 0.497 1.525 5.717 3.519 

2/1/2013 10:54:00 8.879 3.136 1.619 2.841 13.222 26.978 146.066 

2/1/2013 10:55:00 17.478 1.961 1.315 1.465 13.285 27.493 172.625 

2/ 1/2013 10:56:00 20.743 0.249 0.011 0.235 13.271 28.03 153.822 

2/ 1/ 2013 10:57:00 20.805 0.215 -0.001 0.113 13.258 28.132 158.558 

2/1/2013 10:58:00 20.812 0.212 -0.004 0.109 13.258 28.333 151.66 

2/1/2013 10:59:00 20.797 0.22 -0.007 0.133 13.262 28.616 144.756 

2/1/2013 11:00:00 20.782 0.23 0.003 0.108 13.245 29.028 126.426 

2/1/2013 11:01:00 20.549 0.227 -0.002 0.127 13.273 28.914 124.859 

2/1/2013 11:02 :00 20.683 0.259 0.026 0.158 13.292 29.29 105.533 

2/1/2013 11:03:00 19.888 0.33 0.061 0.251 13.276 29.272 96.092 

2/1/2013 11:04:00 16.876 2.616 1.291 0.537 13.275 29.404 90.405 

2/1/2013 11:05:00 13.44 4.505 2.544 1.696 13.311 28.948 103.931 

2/1/2013 11:06:00 13.44 4.505 2.647 1.73 13.308 28.739 107.595 

2/ 1/ 2013 11:07:00 13.433 4.516 2.65 2.014 13.3 29.032 115.202 

2/ 1/ 2013 11:08:00 13.432 4.519 2.754 1.639 13.296 29.5 92.548 

2/1/ 2013 11:09:00 13.44 4.512 2.678 1.341 13.326 29.445 74.547 

2/1/2013 11:10:00 13.45 4.51 2.549 1.393 13.322 28.71 94.037 

2/1/2013 11:11:00 13.441 4.515 2.666 1.715 13.315 29.232 95.323 

2/ 1/2013 11:12:00 13.438 4.517 2.74 1.627 13.297 28.867 101.647 

2/1/2013 11:13:00 13.445 4.513 2.738 1.743 13.323 29.024 100.126 

2/1/2013 11:14:00 13.452 4.513 2.719 1.627 13.313 29.298 95.121 

2/1/2013 11:15:00 13.45 4.515 2.753 1.727 13.321 29.22 98.681 

2/1/2013 11:16:00 13.444 4.52 2.762 1.439 13.313 29.312 87.169 

2/1/2013 11:17:00 13.437 4.524 2.703 1.539 13.3 29.061 99.09 

2/ 1/2013 11:18:00 13.44 4.522 2.556 1.76 13.328 29.128 105.Q13 

2/1/2013 11:19:00 13.437 4.521 2.675 1.605 13.321 29.179 99.934 

2/1/2013 11:20:00 13.438 4.521 2.731 1.488 13.318 29.27 99.652 

2/1/2013 11:21:00 14.263 3.954 2.553 1.57 13.32 28.731 110.723 

2/1/2013 11:22:00 16.522 2.82 1.478 0.88 13.324 29.076 113.878 

2/1/2013 11:23:00 13.423 4.531 2.767 1.518 13.326 29.051 101.824 

2/ 1/ 2013 11:24:00 13.425 4.532 2.76 1.669 13.323 29.085 107.064 

2/ 1/ 2013 11:25:00 13.418 4.537 2.836 1.564 13.322 28.807 106.946 

2/1/2013 11:26:00 13.416 4.537 2.772 1.692 13.318 28.66 112.242 

2/1/2013 11:27:00 13.41 4.543 2.861 1.909 13.324 28.553 126.77 

2/1/2013 11:28:00 13.406 4.545 2.893 1.693 13.319 29.602 97.873 

2/ 1/2013 11:29:00 13.405 4.547 2.868 1.159 13.311 29.828 78.667 

2/1/2013 11:30:00 13.404 4.545 2.842 1.095 13.318 29.477 78.114 

2/1/ 2013 11:31:00 13.407 4.541 2.815 1.273 13.325 29.351 88.364 

2/1/2013 11:32:00 13.418 4.534 2.751 1.317 13.323 29.425 92.317 

2/1/2013 11:33:00 13.409 4.541 2.917 1.17 13.319 29.804 67.984 

2/1/2013 11:34:00 13.405 4.543 2.667 0.945 13.32 29.601 68.443 

2/ 1/ 2013 11:35:00 13.407 4.543 2.702 1.005 13.318 29.464 70.408 

2/1/2013 11:36:00 13.412 4.543 2.667 1.09 13.327 28.981 84.936 

2/1/2013 11:37:00 13.413 4.543 2.734 1.152 13.33 29.358 78.027 

2/1/2013 11:38:00 13.41 4.546 2.795 1.083 13.319 29.185 80.67 

2/1/2013 11:39:00 20.024 0.603 0.425 0.544 13.311 29.216 89.168 

2/ 1/ 2013 11:40:00 14.942 3.757 1.923 0.803 13.313 29.651 81.067 

2/ 1/2013 11:41:00 13.433 4.53 2.634 1.259 13.306 29.747 71.586 

2/ 1/2013 11:42:00 13.423 4.542 2.771 1.103 13.315 29.959 62.751 

THe 

PPM 

-0.013 W bias 

6.928 

16.31 

35.366 Direct Span 

40.348 

41.59 

41.766 

38.476 Direct Zero 

40.183 

45.906 

44.195 

37.09 

39.109 

36.433 

34.061 

28.217 

30.311 

24.159 

21.354 

18.882 

25.546 

26.957 

30.19 

21.102 

13.655 

22.019 

20.86 

24.023 

23.144 

21.555 

22.929 

18.653 

23.474 

24.077 

23.17 

23.815 

27.971 

29.842 

23.389 

25.849 

26.343 

28.279 

33.989 

21.071 

16.033 

15.8 

19.965 

22.339 

11.727 

13.155 

13.872 

19.335 

16.474 

17.117 

19.62 

17.74 

14.101 

10.544 
~ ~ N~ W ~ ~ W 

Date Time % % PPM PPM % PPM PPM 

2/1/2013 11:43:00 13.428 4.537 2.672 1.039 13.318 29.643 66.384 

2/1/2013 11:44:00 13.423 4.543 2.676 1.098 13.3 30.182 59.793 

2/1/2013 11:45:00 13.422 4.546 2.609 0.949 13.316 30.139 55.33 

2/ 1/2013 11:46:00 13.428 4.539 2.512 0.97 13.318 30.185 56.124 

2/ 1/ 2013 11:47:00 13.427 4.539 2.687 0.853 13.315 30.395 48.409 

2/1/2013 11:48:00 13.43 4.539 2.646 0.848 13.318 30.291 48.56 

2/1/2013 11:49:00 13.431 4.539 2.81 0.871 13.322 30.328 46.691 

2/1/2013 11:50:00 13.434 4.541 2.704 0.821 13.309 30.457 45.08 

2/1/2013 11:51:00 13.429 4.543 2.808 0.812 13.31 30.413 44.597 

2/1/2013 11:52:00 13.428 4.547 2.76 0.761 13.315 30.586 42.47 

2/1/2013 11:53:00 13.424 4.552 2.658 0.754 13.307 30.513 43.225 

2/ 1/2013 11:54:00 13.417 4.561 2.651 0.662 13.315 30.621 39.274 

2/1/2013 11:55:00 13.413 4.567 2.707 0.507 13.309 30.764 33.251 

2/1/2013 11:56:00 13.411 4.57 2.736 0.522 13.305 30.707 35.344 

2/1/2013 11:57:00 13.407 4.571 2.667 0.497 13.315 30.649 34.69 

2/1/2013 11:58:00 14.571 3.798 2.308 0.444 13.297 30.906 30.496 

2/1/2013 11:59:00 18.044 1.961 0.905 0.103 13.285 31.216 25.652 

2/1/2013 12:00:00 13.407 4.571 2.635 0.135 13.294 31.017 22.081 

2/1/2013 12:01:00 13.391 4.582 2.615 0.187 13.3 30.847 23.7 

2/1/2013 12:02:00 13.392 4.587 2.573 0.23 13.308 30.822 25.729 

2/ 1/2013 12:03:00 13.401 4.583 2.548 0.217 13.3 31.002 23.716 

2/1/2013 12:04:00 13.381 4.595 2.643 0.185 13.293 31.122 21.546 

2/ 1/2013 12:05:00 13.387 4.594 2.671 0.16 13.292 31.162 20.933 

2/1/2013 12:06:00 13.382 4.602 2.784 0.183 13.291 31.023 24.653 

2/1/2013 12:07:00 13.36 4.615 2.848 0.125 13.27 31.403 21.163 

2/1/2013 12:08:00 13.365 4.614 2.6 0.102 13.303 31.075 20.389 

2/1/2013 12:09:00 13.378 4.61 2.622 0.129 13.287 31.133 21.551 

2/1/2013 12:10:00 13.372 4.615 2.726 0.128 13.278 31.061 22.458 

2/ 1/2013 12:11:00 13.384 4.605 2.733 0.171 13.294 31.108 21.938 

2/1/2013 12:12:00 13.381 4.608 2.862 0.145 13.277 31.323 19.982 

2/ 1/ 2013 12:13:00 13.391 4.6 2.618 0.158 13.3 31.034 20.528 

2/1/2013 12:14:00 13.394 4.602 2.576 0.153 13.297 31.069 20.7 

2/1/2013 12:15:00 13.39 4.608 2.724 0.147 13.298 31.146 20.316 

2/1/2013 12:16:00 12.997 4.405 2.275 0.194 10.901 13.98 18.766 

2/1/2013 12: 17 :OO ! .. -:1:;;0.71::;15~--:5:;".3;;:1::-7 --.0::'.0:;0';5! .0.192 !.....:7 .. 9.:;;9:;32:--:1:::.1"'2;2! 1.203 

2/1/2013 12:18:00 9.974 5.232 0.007 -0.378 4.708 11.986 -0.324 

2/1/2013 12:19:00 0.538 0.308 4.409 -0.024 0.052 24.97 -0.162 

2/1/2013 12:20:00"!-";0".1"9::-8 -"';;0."'2':::46;--4;';. 7,;;0;;;7,-.....;0".1;;;5.;.1-....;:,0:;;.~03;-~24;...;;;95;.;9,-.....;.0;;;.1::6:;3! 

2/ 1/2013 12:21:00 0.193 0.239 4.143 0.323 0.026 12.789 22.863 

2/1/2013 12:22:00 0.173 0.234 -0.012 3.849 0.022 0.752 118.41 

2/1/2013 12:23:00 0.168 0.231 ·0.Q25! 4.426! 0.022 0.663 124.871 

2/1/2013 12:24:00 7.873 4.385 2.949 4.438 5.629 11.237 128.216 

2/1/2013 12:25:00 10.048 5.34 4.745 4.437 10.196 18.086 130.491 

2/1/2013 12:26:00 .. !......;'-:1-:i0.':i0~6--5"'.;;.34:--4;.;7;,,4;;:7,---:4.;,.4;;:3.;,,2! 3.387 9.578 78.151 

2/ 1/2013 12:27:00 6.632 3.459 3.525 4.122 0.033 0.65 136.832 

2/1/2013 12:28:00 0.107 0.202 -0.024 0.367 0.023 0.562! 137.709! 

2/1/2013 12:29:00 0.094 0.2 -0.03 -0.029 0.022 0.513 137.992 

2/ 1/ 2013 12 30 00"!-";0";0:;:9';'4-~0-:1;;;99;-""".0":0;;;3;;;6--.";0".0;;:2; 2! 0.025 0.403 132.935 

2/ 1/2013 12:31:00 0.178 0.234 -0.024 1.117 0.022 0.126 19.789 

2/1/2013 12:32:00 5.681 2.224 0.884 3.435 0.022 0.122 -0.212 

2/1/2013 12:33:00 15.578 0.507 0.34 0.68"!-'::0";.0"'2::-3 -"';;0.710~5;-""";.0::'.2:;1:;7! 

2/1/2013 12:34:00 13.308 0.266 -0.02 0.389 8.24 17.559 45.347 

2/1/2013 12:35:00 20.301 0.27 -0.022 0.108 9.94 24.433 137.256 

2/ 1/ 2013 12:36:00 2.46 0.235 -0.032 0.038!" -";:9""9~4';'1-~24';'47.5;-';;1;'38';'.2;;;1:;2! 

2/ 1/ 2013 12:37:00 0.199 0.233 -0.029 -0.002 11.561 24.126 108.912 

2/ 1/ 2013 12:38:00 0.176 0.232 -0.033 -0.001 13.289 29.92 30.7 

2/1/2013 12:39:00 0.168 0.233 -0.03 -0.012 13.292 29.961 27.137 

2/1/2013 12:40:00 0.167 0.233 -0.028 -0.008 13.292 30.151 29.546 

THC 

PPM 

12.494 

9.953 

9.305 

9.505 

6.858 

7.219 

6.857 

6.448 

6.132 

5.524 

5.82 

4.627 

2.752 

3.5 

3.314 

2.396 

1.393 

0.826 

1.135 

1.326 

1.137 

0.71 

0.57 

1.462 

0.672 

0.634 

0.827 

1 

0.779 

0.518 

0.53 

0.606 

0.563 

0.476 

·0.Q2 02/C02 bias 

-0.02 

-0.021 

-0.02 NOx bias 

-0.019 

-0.015 

-0.015 W bias 

0.133 

1.359 

0.493 Direct Span 

-0.015 

-0.014 Inlet CO bias 

-0.014 

-0.014 Zero Direct 

0.571 

0.911 

0.919 Zero Direct 

0.909 

1.005 

1.101 Span Direct 

0.9 

1.267 

0.95 

1.745 
Date Time 

2/1/2013 12:41:00 

2/1/2013 12:42:00 

2/1/2013 12:43:00 

2/ 1/2013 12:44:00 

2/ 1/ 2013 12:45:00 

2/1/ 2013 12:46:00 

2/1/2013 12:47:00 

2/1/2013 12:48:00 

2/1/2013 12:49:00 

2/1/2013 12:50:00 

2/1/2013 12:51:00 

2/1/2013 12:52:00 

2/ 1/ 2013 12:53:00 

2/1/2013 12:54:00 

2/1/2013 12:55:00 

2/1/2013 12:56:00 

2/1/2013 12:57:00 

2/1/2013 12:58:00 

2/1/2013 12:59:00 

2/1/2013 13:00:00 

2/ 1/2013 13:01:00 

2/1/2013 13:02:00 

2/1/2013 13:03:00 

2/ 1/2013 13:04:00 

2/1/2013 13:05:00 

2/1/2013 13:06:00 

2/1/2013 13:07:00 

2/1/2013 13:08:00 

2/1/2013 13:09:00 

2/1/2013 13:10:00 

2/ 1/ 2013 13:11:00 

2/1/2013 13:12:00 

2/1/2013 13:13:00 

2/1/2013 13:14:00 

2/1/2013 13:15:00 

2/1/2013 13:16:00 

2/1/2013 13:17:00 

2/1/2013 13:18:00 

2/ 1/ 2013 13:19:00 

2/1/2013 13:20:00 

2/ 1/2013 13:21:00 

2/1/2013 13:22:00 

2/1/2013 13:23:00 

2/1/2013 13:24:00 

2/1/2013 13:25:00 

2/1/2013 13:26:00 

2/ 1/ 2013 13:27:00 

2/ 1/ 2013 13:28:00 

2/1/2013 13:29:00 

2/1/2013 13:30:00 

2/1/2013 13:31:00 

2/1/2013 13:32:00 

2/1/2013 13:33:00 

2/ 1/ 2013 13:34:00 

2/1/2013 13:35:00 

2/1/ 2013 13:36:00 

2/1/2013 13:37:00 

2/1/2013 13:38:00 

2/1/2013 13:39:00 

0, 

% 

0.168 

0.168 

0.148 

0.143 

0.143 

0.143 

0.143 

0.143 

0.306 

0.575 

0.688 

0.784 

0.873 

0.957 

0.792 

0.936 

1.034 

1.12 

1.168 

1.217 

1.213 

1.005 

1.039 

1.073 

1.098 

1.136 

1.146 

1.164 

1.181 

1.201 

1.224 

1.24 

1.266 

1.298 

1.313 

1.328 

1.344 

1.363 

1.37 

1.384 

1.384 

1.385 

1.386 

1.388 

1.402 

1.403 

1.412 

1.389 

1.352 

1.302 

1.255 

1.211 

1.152 

1.032 

1.009 

0.528 

0.282 

0.334 

0.08 

CO2 NO. CO 

% PPM PPM 

0.234 -0.031 0.002 

0.234 -0.027 -0.01 

0.235 -0.036 -0.01 

0.235 -0.034 -0.003 

0.236 -0.034 -0.008 

0.235 -0.031 -0.013 

0.236 -0.036 -0.015 

0.237 -0.034 -0.005 

0.238 -0.032 -0.005 

0.238 -0.035 -0.Q1 

0.238 -0.037 -0.023 

0.238 -0.034 -0.02 

0.239 -0.029 -0.01 

0.24 -0.034 -0.018 

0.241 -0.035 -0.012 

0.242 -0.04 -0.Q15 

0.242 -0.04 -0.Q15 

0.244 -0.039 -0.016 

0.244 -0.036 -0.007 

0.245 -0.036 -0.009 

0.374 0.027 -0.039 

0.523 0.124 -0.055 

0.535 0.128 -0.Q7 

0.546 0.136 -0.073 

0.556 0.14 -0.067 

0.569 0.149 -0.06 

0.575 0.157 -0.077 

0.581 0.158 -0.077 

0.588 0.169 -0.066 

0.594 0.176 -0.074 

0.602 0.176 -0.073 

0.61 0.181 -0.067 

0.62 0.204 -0.073 

0.628 0.189 -0.081 

0.635 0.188 -0.073 

0.642 0.199 -0.073 

0.648 0.205 -0.073 

0.655 0.203 -0.085 

0.659 0.213 -0.084 

0.662 0.212 -0.062 

0.664 0.21 -0.072 

0.664 0.212 -0.072 

0.667 0.219 -0.071 

0.669 0.203 -0.068 

0.672 0.212 -0.Q75 

0.675 0.218 -0.08 

0.678 0.216 -0.058 

0.672 0.208 -0.064 

0.664 0.205 -0.073 

0.647 0.198 -0.062 

0.632 0.188 -0.073 

0.618 0.177 -0.064 

0.601 0.161 -0.076 

0.561 0.135 -0.061 

0.554 0.133 -0.07 

0.39 0.054 -0.059 

0.319 -0.005 -0.032 

0.342 0.008 -0.041 

0.263 -0.02 -0.049 

0 , 

% 

13.282 

13.284 

13.29 

13.283 

13.286 

13.265 

13.272 

13.273 

13.264 

13.26 

13.274 

13.26 

13.258 

13.253 

13.249 

13.247 

13.244 

13.266 

13.257 

13.248 

13.243 

13.242 

13.261 

13.266 

13.27 

13.26 

13.271 

13.262 

13.269 

13.278 

13.27 

13.237 

13.28 

13.271 

13.273 

13.261 

13.254 

13.255 

13.256 

13.28 

13.264 

13.264 

13.27 

13.276 

13.278 

13.265 

13.289 

13.28 

13.281 

13.282 

13.29 

13.289 

13.286 

13.282 

13.279 

13.281 

13.282 

13.27 

4.02 

NO~ CO 

PPM PPM 

30.381 28.247 

30.407 25.479 

30.388 25.708 

30.465 25.35 

30.521 26.25 

30.865 23.928 

30.789 23.788 

30.622 25.66 

30.903 24.949 

30.979 22.606 

30.872 22.99 

30.948 23.319 

31.045 23.152 

31.036 23.737 

31.066 23.175 

31.062 22.786 

31.141 22.617 

30.925 22.482 

30.953 22.995 

31.046 22.8 

31.16 22.627 

31.24 22.036 

30.892 23.386 

30.889 23.521 

31.015 22.939 

31.06 22.636 

30.875 23.276 

30.869 23.667 

30.885 24.595 

30.849 23.813 

30.897 23.461 

31.248 22.488 

30.837 23.364 

30.956 22.692 

30.915 23.363 

30.969 22.598 

30.935 23.39 

30.905 23.417 

30.937 23.316 

30.784 23.984 

30.943 23.269 

31.047 22.459 

30.996 22.382 

30.932 22.652 

30.892 23.323 

30.936 23.094 

30.8 23.021 

30.75 23.436 

30.696 23.796 

30.662 24.775 

30.627 24.327 

30.591 24.6 

30.589 23.919 

30.772 23.676 

30.775 23.514 

30.67 24.026 

30.745 24.01 

30.694 25.236 

12.248 18.546 

THe 

PPM 

1.319 

0.89 

0.887 

0.822 

1.15 

0.85 

0.734 

1.097 

1.004 

0.565 

0.562 

0.542 

0.598 

0.807 

0.633 

0.563 

0.586 

0.415 

0.499 

0.565 

0.488 

0.524 

0.69 

0.701 

0.548 

0.478 

0.643 

0.594 

0.92 

0.597 

0.567 

0.388 

0.529 

0.459 

0.546 

0.498 

0.557 

0.555 

0.463 

0.625 

0.519 

0.503 

0.539 

0.42 

0.517 

0.575 

0.462 

0.52 

0.588 

0.758 

0.645 

0.676 

0.613 

0.523 

0.574 

0.604 

0.597 

0.854 

1.289 
~ ~ N~ W 0 , ~ W 

Date Time % % PPM PPM % PPM PPM 

2/1/2013 13:40:00 0.067 0.249 -0.039 -0.037 0.027 0.236 0.371 

2/1/2013 13:41 00!r--::0;';:.0~67':--0';;.;:'24;';9:----:0;;'0~3~4--;';:0;';:.0~31:---0';;."'02~2~--:0;;'.1~9::'5---;';:O:':. 2~4~1! 

2/ 1/2013 13:42:00 7.48 4.125 2.91 1.669 5.859 12.673 19.848 

2/ 1/ 2013 13:43:00 10.036 5.399 4.729 4.364 9.939 24.548 131.984 

2/ 1/ 2013 13 44 oo!r--:1':::0;';:0~44:---5~.~40;::1~~4:". 7;':3:;:2---;4-:.4':;'38::--":9~9':':~"";;'2:'::4'";5";3-;;';1~3i:8";2::18! 

2/ 1/ 2013 13:45:00 6.368 2.782 2.189 3.071 11.528 23.706 102.634 

2/1/ 2013 13:46:00 12.36 4.679 2.099 0.312 9.954 5.69 18.338 

2/1/ 2013 13:4 oo!r-"':'1;:;0~04:-;3~"""';'5-:. 3';;:85;---;0;;'0~1';;19! 316!r-~9~9~175 --'1:-':.0:;';3';'1! -0.413 

2/1/2013 13:48:00 10.047 5.39 -0.024 -0.395 10.648 5.104 0.454 

2/1/2013 13:49:00 11.597 5.034 1.14 -0.213 13.258 29.795 26.289 

2/1/2013 13:50:00 12.56 4.46 2.447 0.195 3.516 26.346 15.941 

2/ 1/2013 13:51:00 0.401 0.342 4.597 0.087 0.046 24.945 0.042 

2/ 1/ 2013 13:52:00 !r--::0'";1':;'73:---0';;~30:::5'-~4:;;. 7;;:1~1-""';;:i'0.~14':--0';;"'02;':2~-2~4:':8~7:;:7---;';:0-:1-';78::'! 

2/ 1/ 2013 13:53:00 0.166 0.298 4.72 0.148 0.022 12.522 28.964 

2/ 1/ 2013 13:54:00 0.16 0.294 0.63 2.872 0.021 0.732 132.022 

2/ 1/2013 13:55:00 0.142 0.292 -0.026! 4.385! 0.02 0.643! 135.873! 

2/ 1/2013 13:56:00 0.142 0.29 -0.032 4.4 6.599 13.314 117.599 

2/1/2013 13:57:00 9.674 3.638 1.927 2.357 13.241 30.06 29.213 

2/ 1/2013 13:58:00 13.315 4.667 2.688 0.22 13.265 30.137 23.578 

2/ 1/ 2013 13:59:00 13.331 4.678 2.602 0.176 13.263 30.28 26.534 

2/ 1/2013 14:00:00 13.334 4.681 2.618 0.195 13.269 30.174 25.532 

2/ 1/2013 14:01:00 13.35 4.677 2.589 0.205 13.382 29.597 25.495 

2/1/ 2013 14:02:00 13.521 4.571 2.072 0.19 13.733 26. 369 36.519 

2/ 1/2013 14:03 :00 14.188 4.173 2.094 0.212 13.738 26.427 40.596 

2/ 1/ 2013 14:04:00 14.458 4.027 1.752 0.316 13.734 26.718 38.895 

2/1/2013 14:05:00 14.464 4.024 1.654 0.305 13.734 26.793 38.323 

2/1/2013 14:06:00 14.453 4.032 1.575 0.305 13. 728 26.884 38.238 

2/ 1/ 2013 14:07:00 14.438 4.044 1.629 0.31 13.747 26.766 38.982 

2/ 1/ 2013 14:08:00 14.446 4.041 1.557 0.315 13.763 26.715 39.302 

2/1/ 2013 14:09:00 14.442 4.047 1.511 0.321 13.746 26.921 38.996 

2/ 1/ 2013 14:10:00 14.407 4.068 1.576 0.297 13. 752 26.731 38.796 

2/ 1/ 2013 14:11:00 14.424 4.06 1.499 0.306 13.756 26.56 40.469 

2/ 1/ 2013 14:12:00 14.416 4.064 1.487 0.317 13.741 26.817 39.398 

2/1/2013 14:13:00 14.396 4.075 1.736 0.293 13.758 26.631 39.535 

2/1/2013 14:14:00 14.406 4.073 1.697 0.311 13.758 26.596 40.907 

2/ 1/ 2013 14:15:00 14.415 4.079 1.67 0.318 13.734 26.935 39.391 

2/ 1/ 2013 14:16:00 14.388 4.098 1.801 0.293 13.733 26.953 39.025 

2/ 1/ 2013 14:17:00 14.368 4.11 1.844 0.285 13.723 27.216 37.853 

2/ 1/ 2013 14:18:00 14.372 4.109 1.799 0.259 13.738 26.964 38.309 

2/ 1/ 2013 14:19:00 14.395 4.099 1.68 0.303 13.744 26.985 39.072 

2/1/ 2013 14:20:00 14.379 4.109 1.751 0.288 13.737 27.115 38.18 

2/ 1/2013 14:21:00 14.364 4.112 1.941 0.271 13.739 27.104 37.882 

2/1/2013 14:22:00 14.373 4.106 1.949 0.274 13.756 26.95 38.289 

2/ 1/2013 14:23:00 14.397 4.095 1.798 0.288 13.768 26.752 39.693 

2/1/ 2013 14:24:00 14.394 4.098 1.759 0.299 13.761 26.95 39.194 

2/ 1/2013 14:25:00 14.383 4.104 1.854 0.284 13.76 27.018 38.333 

2/1/2013 14:26:00 14.368 4.11 1.937 0.251 13.768 26.875 39.191 

2/ 1/ 2013 14:27:00 14.368 4.108 1.909 0.246 13.773 26.847 39.739 

2/1/ 2013 14:28:00 14.363 4.113 1.918 0.223 13.766 27.01 38.604 

2/ 1/ 2013 14:29:00 14.363 4.111 1.995 0.214 13.776 26.912 38.716 

2/1/2013 14:30:00 14.372 4.101 1.866 0.222 13.766 27.001 38.914 

2/ 1/2013 14:31:00 14.366 4.103 2.007 0.235 13.78 26.826 39.202 

2/ 1/ 2013 14:32:00 14.38 4.093 2.048 0.274 13.773 26.865 40.37 

2/ 1/ 2013 14:33:00 14.371 4.098 2.309 0.261 13.784 26.862 39.48 

2/1/ 2013 14:34:00 14.382 4.087 1.847 0.244 13.773 27.017 39.234 

2/ 1/ 2013 14:35:00 14.359 4.097 2.148 0.247 13.762 27.12 38.314 

2/ 1/ 2013 14:36:00 14.367 4.088 2.346 0.247 13.771 26.977 39.315 

2/1/ 2013 14:37:00 16.409 2.892 1.614 0.214 13.767 27.141 38.612 

THC 

PPM 

0.667 

0.577 Direct Zero 

0.575 

0.723 Span Direct 

0.554 Span Direct 

1.054 

0.3 

-0.023 0 2/C02 bias 

-0.021 

2.206 

0.367 

-0.022 

-0.022 NOx bias 

-0.021 

-0.017 

-0.017 CO bias 

0.022 

0.49 

0.452 

1.028 

0.785 

0.817 

1.352 

1.479 

1.312 

1.195 

1.162 

1.372 

1.43 

1.468 

1.493 

1.581 

1.295 

1.252 

1.553 

1.438 

1.393 

1.335 

1.3 

1.456 

1.239 

1.32 

1.341 

1.475 

1.386 

1.337 

1.473 

1.511 

1.405 

1.345 

1.313 

1.378 

1.573 

1.397 

1.311 

1.239 

1.39 

1.387 
Date Time 

2/ 1/ 2013 14:38:00 

2/1/ 2013 14:39:00 

2/ 1/ 2013 14:40:00 

2/1/2013 14:41:00 

2/1/2013 14:42:00 

2/1/2013 14:43:00 

2/ 1/ 2013 14:44:00 

2/ 1/ 2013 14:45:00 

2/1/2013 14:46:00 

2/1/2013 14:47:00 

2/1/2013 14:48:00 

2/1/ 2013 14:49:00 

2/1/ 2013 14:50:00 

2/ 1/ 2013 14:51:00 

2/1/2013 14:52:00 

2/1/2013 14:53:00 

2/1/ 2013 14:54:00 

2/ 1/ 2013 14:55:00 

2/ 1/ 2013 14:56:00 

2/1/2013 14:57:00 

2/1/2013 14:58:00 

2/1/2013 14:59:00 

2/1/ 2013 15:00:00 

2/1/2013 15:01:00 

2/ 1/ 2013 15:02:00 

2/1/2013 15:03:00 

2/1/2013 15:04:00 

2/1/2013 15:05:00 

2/ 1/ 2013 15:06:00 

2/ 1/ 2013 15:07:00 

2/1/ 2013 15:08:00 

2/1/2013 15:09:00 

2/1/2013 15:10:00 

2/ 1/ 2013 15:11:00 

2/1/ 2013 15:12:00 

2/ 1/2013 15:13:00 

2/1/2013 15:14:00 

2/1/2013 15:15:00 

2/1/2013 15:16:00 

2/ 1/2013 15:17:00 

2/ 112013 15:18:00 

2/1/2013 15:19:00 

2/1/2013 15:20:00 

2/1/2013 15:21:00 

2/ 1/ 2013 15:22:00 

2/ 1/ 2013 15:23:00 

2/ 1/ 2013 15:24:00 

2/1/2013 15:25:00 

2/1/2013 15:26:00 

2/1/ 2013 15:27:00 

2/ 1/ 2013 15:28:00 

2/ 1/ 2013 15:29:00 

2/1/2013 15:30:00 

2/1/2013 15:31:00 

2/1/2013 15:32:00 

2/1/ 2013 15:33:00 

2/ 1/ 2013 15:34:00 

2/ 1/ 2013 15:35:00 

2/1/2013 15:36:00 

0 , 

% 

14.411 

14.38 

14.38 

14.382 

14.385 

14.392 

14.385 

14.387 

14.391 

14.375 

14.377 

14.368 

14.341 

14.306 

14.308 

14.299 

14.304 

15.137 

18.098 

14.346 

14.343 

14.336 

14.344 

14.344 

14.35 

14.345 

14.342 

14.349 

14.345 

14.344 

14.345 

14.348 

14.342 

14.342 

14.348 

14.349 

14.344 

14.346 

14.345 

14.455 

20.379 

15.877 

14.399 

14.398 

14.391 

14.39 

14.392 

14.398 

14.421 

14.434 

14.427 

14.44 

14.427 

14.437 

14.44 

14.462 

14.452 

14.465 

14.454 

CO2 NOx CO 

% PPM PPM 

4.071 2.283 0.304 

4.077 2.21 0.379 

4.077 2.178 0.389 

4.076 2.227 0.387 

4.076 2.201 0.392 

4.072 2.127 0.386 

4.074 2.166 0.386 

4.075 2.18 0.4 

4.072 2.155 0.424 

4.083 2.263 0.405 

4.081 2.253 0.397 

4.082 2.19 0.417 

4.098 2.38 0.395 

4.123 2.492 0.329 

4.119 2.426 0.343 

4.124 2.382 0.338 

4.124 2.437 0.328 

3.597 2.161 0.328 

1.951 0.819 0.166 

4.086 2.318 0.444 

4.094 2.309 0.418 

4.102 2.395 0.398 

4.095 2.355 0.391 

4.096 2.309 0.391 

4.094 2.286 0.402 

4.098 2.247 0.402 

4.104 2.314 0.397 

4.093 2.259 0.403 

4.101 2.256 0.422 

4.1 2.27 0.406 

4.097 2.267 0.405 

4.097 2.236 0.392 

4.106 2.404 0.394 

4.106 2.47 0.379 

4.099 2.219 0.406 

4.096 2.417 0.388 

4.101 2.333 0.379 

4.1 2.326 0.375 

4.103 2.206 0.393 

4.047 2.31 0.357 

0.541 0.159 0.113 

3.263 1.438 0.203 

4.069 2.036 0.377 

4.071 2.106 0.36 

4.077 2.197 0.353 

4.075 2.127 0.367 

4.073 2.109 0.365 

4.07 2.081 0.385 

4.057 2.041 0.399 

4.053 1.976 0.413 

4.057 2.056 0.396 

4.05 2.012 0.418 

4.055 2.072 0.408 

4.048 2.083 0.4 

4.043 1.937 0.385 

4.031 1.771 0.379 

4.037 1.883 0.383 

4.03 1.856 0.385 

4.037 1.841 0.384 

O2 NOx CO THC 

% PPM PPM PPM 

13.766 27.181 38.384 1.421 

13.765 27.174 38.359 1.402 

13.763 27. 231 38.224 1.446 

13.766 27.153 38.161 1.375 

13.77 27.149 37.983 1.189 

13.773 27.159 38.242 1.308 

13.776 27.08 38.126 1.369 

13.777 27.065 38.494 1.366 

13.775 27.113 38.466 1.311 

13.763 27.286 37.651 1.181 

13.769 27. 161 37.782 1.243 

13.76 27.208 38.142 1.233 

13.746 27.345 37.251 1.058 

13.761 27.22 37.407 1.126 

13.758 27.083 38.494 1.199 

13.748 27.279 37.513 1.27 

13.747 27.191 37.852 1.277 

13.761 27.064 38.333 1.22 

13.738 27.154 38.248 1.271 

13.738 27.292 37.668 1.258 

13.738 27.321 37.237 1.17 

13.731 27.398 36.738 1.133 

13.738 27.282 37.283 1.18 

13.741 27.303 37.323 1.215 

13.749 27.16 37.82 1.341 

13.749 27.145 38.137 1.365 

13.744 27.248 37.516 1.282 

13.755 27.084 38.054 1.378 

13.741 27.174 38.146 1.374 

13.756 27.057 38.464 1.394 

13.763 27.067 38.588 1.439 

13.744 27.262 38.266 1.278 

13.738 27 .389 36.944 1.119 

13.747 27.242 37.471 1.259 

13.757 27 .083 38.553 1.397 

13.754 27.129 38.348 1.331 

13.732 27.326 37.732 1.287 

13.742 27.238 37.566 1.158 

13.736 27.395 37.278 1.108 

13.73 27.553 36.444 1.042 

13.739 27.38 36.422 1.149 

13.732 27.421 37.242 1.12 

13.727 27.555 35.902 0.944 

13.722 27.643 35.563 0.959 

13.733 27.532 35.75 0.953 

13.734 27.582 35.904 1.089 

13.747 27.51 36.075 1.091 

13.734 27.584 36.084 1.144 

13.756 27.373 36.662 1.175 

13.738 27.533 36.441 1.105 

13.748 27.469 36.331 0.99 

13.751 27.408 36.565 1.171 

13.731 27.576 36.39 1.236 

13.747 27.493 36.357 1.176 

13.76 27.385 36.692 1.163 

13.749 27.422 36.805 1.226 

13.755 27.465 36.29 1.044 

13.757 27.354 37.083 1.056 

13.754 27.386 37.038 1.213 
~ ~ N~ 00 ~ N~ 00 

Date Time % % PPM PPM % PPM PPM 

2/1/2013 15:37:00 14.449 4.039 1.875 0.389 13.762 27.327 37.305 

2/1/2013 15:38:00 11.913 3.293 1.632 0.621 4.547 11.392 65.329 

2/1/2013 15:39:00 0.302 0.313 -0.02 3.884 0.05 1.064 133.833 

2/1/2013 15:40:00 0.217 0.296 -0.026! 4.385! 0.034 0.927! 135.334! 

2/1/2013 15:41:00 2.078 1.389 -0.035 4.129 6.134 0.864 101.253 

2/1/2013 15:42 :00 f"!--;l';;'0.';;'03~2:-""';;~.';' 36~~0::-:.0~3;;'1! 0.136f"! -9;;-9;;';1~3-~0~8;-;1716! 3.211 

2/1/2013 15:43:00 7.117 3.768 1.201 -0.348 4.839 11.589 -0.161 

2/1/2013 15:44:00 f"! -~O-;. 2~1::"2 --.;;.0.'i:30i:'7:----'4:-'.6:i:9:-;2:-.....:.;;0.;;.0~8 --;::-0 . .;;.04~1:-~24:-.6~8;:;8----;0:';.1~2i'15! 

2/1/2013 15:45:00 0.175 0.279 2.533 0.106 0.05 7.262 -0.116 

2/1/2013 15:46:00 0.093 0.252 -0.032 -0.032 0.022 0.184 -0.216 

2/1/2013 15:47:00f"! --;:0-;.0:i;93i:--:;'0.';'25;';1:-~-0~.0i:'3;;:5----;0~.04:::7 4 --';;'0.';;'02;;'2:--~0;-1;-;5";"1---~0:"'. 2;";1:':!9! 

2/1/2013 15:48:00 7.651 4.327 3.157 1.885 5.789 12.262 35.166 

2/1/2013 15:49:00 ...... ..;1:;;0;,:; .0:;,79=-_;;;5.;;;39=:9;.-_4;;.. 7;,;3;.;4_--:,.;4.:;;3;:,9 _...;;;9.;;;95;;;6;.-...,;.24;;.3~9;.;7_1;;;3:;;6;;.2:;;0~1 

2/1/2013 15:50:00! 10.086 5.398 4.742 4.427 9.966 24.424 138.268! 

2/1/2013 15:51:00 6.208 2.448 3.99 2.745 12.214 23.476 99.129 

2/1/2013 15:52:00 14.342 4.003 1.969 0.504 13.758 26.875 40.157 

2/1/2013 15:53:00 14.398 4.051 1.95 0.453 13.763 26.944 39.292 

2/1/2013 15:54:00 14.396 4.056 2.033 0.434 13.75 27.261 37.89 

2/1/2013 15:55:00 14.389 4.062 2.236 0.392 13.764 27.057 38.359 

2/1/2013 15:56:00 14.407 4.054 1.935 0.412 13.761 27.094 38.81 

2/1/2013 15:57:00 14.4 4.06 2.165 0.418 13.762 27.066 38.861 

2/1/2013 15:58:00 14.412 4.056 2.096 0.423 13.766 27.021 39.447 

2/1/2013 15:59:00 14.439 4.039 1.975 0.424 13.769 27.032 39.615 

2/1/2013 16:00:00 14.466 4.025 2.009 0.431 13.785 27.007 39.743 

2/1/2013 16:01:00 14.474 4.02 1.981 0.445 13.783 27.003 39.802 

2/1/2013 16:02:00 14.46 4.028 2.012 0.44 13.764 27.126 39.609 

2/1/2013 16:03:00 14.452 4.03 2.038 0.441 13.765 27.127 39.775 

2/1/2013 16:04:00 14.453 4.027 2.074 0.437 13.764 27.344 38.172 

2/1/2013 16:05:00 14.473 4.017 2.067 0.391 13.761 27.491 37.66 

2/1/2013 16:06:00 14.464 4.019 2.128 0.374 13.786 27.105 38.802 

2/1/2013 16:07:00 14.501 4.003 1.96 0.396 13.764 27.347 39.089 

2/1/2013 16:08:00 14.474 4.014 1.999 0.4 13.761 27.574 37.555 

2/1/2013 16:09:00 14.462 4.018 2.044 0.371 13.764 27.536 37.305 

2/1/2013 16:10:00 17.285 2.259 1.252 0.322 13.771 27.28 38.382 

2/1/2013 16:11:00 20.51 0.591 0.033 0.089 13.764 27.377 38.815 

2/1/2013 16:12:00 14.508 4.036 2.397 0.242 13.764 27.631 37.436 

2/1/2013 16:13:00 14.364 4.068 2.428 0.336 13.764 27.674 36.426 

2/1/2013 16:14:00 14.367 4.068 2.253 0.345 13.76 27.699 36.741 

2/ 1/2013 16:15:00 14.356 4.074 2.373 0.343 13.764 27.547 36.977 

2/1/2013 16:16:00 14.361 4.071 2.267 0.352 13.751 27.681 36.628 

2/1/2013 16:17:00 14.349 4.079 2.331 0.342 13.742 27.711 36.509 

2/1/2013 16:18:00 14.344 4.085 2.44 0.338 13.744 27.783 35.825 

2/1/2013 16:19:00 14.345 4.08 2.395 0.348 13.743 27.776 35.943 

2/1/2013 16:20:00 14.343 4.084 2.381 0.335 13.761 27.71 35.932 

2/1/2013 16:21:00 14.353 4.072 2.343 0.353 13.765 27.458 36.674 

2/1/2013 16:22:00 14.353 4.077 2.306 0.365 13.765 27.344 37.616 

2/1/2013 16:23:00 14.317 4.106 2.389 0.329 13.765 27.398 37.347 

2/1/2013 16:24:00 14.319 4.103 2.486 0.333 13.771 27.403 37.194 

2/1/2013 16:25:00 14.326 4.099 2.373 0.338 13.766 27.423 37.223 

2/1/2013 16:26:00 14.318 4.104 2.402 0.325 13.77 27.431 36.923 

2/1/2013 16:27:00 14.323 4.096 2.39 0.34 13.772 27.575 36.663 

2/1/2013 16:28:00 14.323 4.1 2.405 0.305 13.76 27.726 35.812 

2/1/2013 16:29:00 18.607 1.612 0.867 0.15 13.769 27.579 36.252 

2/1/2013 16:30:00 14.388 4.052 2.372 0.288 13.773 27.415 37.309 

2/1/2013 16:31:00 14.38 4.052 2.285 0.366 13.775 27.506 37.211 

2/1/2013 16:32:00 14.374 4.055 2.285 0.364 13.765 27.613 36.521 

2/1/2013 16:33:00 14.36 4.06 2.369 0.368 13.775 27.414 37.121 

2/1/2013 16:34:00 14.376 4.052 2.311 0.393 13.791 27.353 37.75 

THC 

PPM 

1.237 

0.87 

-0.016 

-0.016 CO bias 

-0.017 

-0.021 02/C02 bias 

-0.021 

-0.021 NOx bias 

0.271 

1.221 

1.257 Direct Zero 

1.269 

1.241 

1.218 Direct Span 

1.404 

1.463 

1.33 

1.174 

1.273 

1.324 

1.352 

1.344 

1.256 

1.286 

1.236 

1.299 

1.332 

1.236 

1.197 

1.227 

1.301 

1.142 

1.156 

1.155 

1.335 

1.139 

1.168 

1.129 

1.223 

1.193 

1.08 

0.986 

1.054 

1.143 

1.145 

1.211 

1.176 

1.258 

1.278 

1.105 

1.198 

1.117 

1.196 

1.252 

1.251 

1.014 

1.115 

1.218 
~ ~ ~ w 0 , N~ W 

Oate Time % % PPM PPM % PPM PPM 

2/1/2013 16:35:00 14.383 4.046 2.326 0.401 13.767 27.549 36.971 

2/1/2013 16:36:00 14.367 4.053 2.394 0.387 13.774 27.57 36.443 

2/1/2013 16:37:00 14.37 4.049 2.32 0.37 13.804 27.334 37.488 

2/ 1/ 2013 16:38:00 14.384 4.039 2.232 0.384 13.809 27.239 38.064 

2/1/2013 16:39:00 14.4 4.028 2.309 0.392 13.81 27.181 38.667 

2/1/2013 16:40:00 14.4 4.025 2.223 0.413 13.794 27.289 38.226 

2/1/2013 16:41:00 14.385 4.03 2.294 0.414 13.783 27.383 37.818 

2/ 1/ 2013 16:42:00 14.37 4.04 2.31 0.4 13.773 27.448 37.199 

2/ 1/ 2013 16:43:00 14.367 4.039 2.392 0.373 13.793 27.282 37.9 

2/1/2013 16:44:00 14.379 4.031 2.266 0.409 13.765 27.506 37.329 

2/1/2013 16:45:00 14.347 4.049 2.369 0.379 13.778 27.355 37.432 

2/ 1/2013 16:46:00 14.369 4.03 2.384 0.394 13.777 27.355 37.657 

2/1/2013 16:47:00 14.369 4.029 2.339 0.415 13.773 27.38 37.679 

2/1/2013 16:48:00 14.365 4.03 2.333 0.388 13.771 27.505 37.079 

2/1/2013 16:49:00 14.36 4.032 2.389 0.387 13.763 27.701 35.826 

2/ 1/ 2013 16:50:00 14.347 4.041 2.473 0.371 13.764 27.498 36.352 

2/ 1/ 2013 16:51:00 18.975 1.241 0.789 0.246 13.777 27.311 37.453 

2/1/2013 16:52:00 15.199 3.677 1.614 0.239 13.803 27.2 38.168 

2/1/2013 16:53:00 14.453 3.973 1.906 0.41 13.796 27.219 38.444 

2/1/2013 16:54:00 14.441 3.977 2.006 0.422 13.764 27.446 37.677 

2/ 1/2013 16:55:00 14.43 3.985 2.103 0.395 13.779 27.321 37.866 

2/1/2013 16:56:00 14.435 3.981 2.071 0.4 13.785 27.249 38.164 

2/1/2013 16:57:00 14.44 3.978 2.008 0.407 13.787 27.218 38.231 

2/ 1/ 2013 16:58:00 14.443 3.974 2.084 0.412 13.81 27.052 39.247 

2/ 1/2013 16:59:00 14.439 3.978 2.158 0.422 13.785 27.163 38.876 

2/1/2013 17:00:00 14.444 3.974 2.177 0.41 13.799 27.17 38.407 

2/1/2013 17:01:00 14.479 3.953 2.164 0.428 13.803 27.06 39.26 

2/ 1/ 2013 17:02:00 14.462 3.959 2.129 0.444 13.795 27.077 39.083 

2/1/2013 17:03:00 14.471 3.952 2.106 0.449 13.783 27.135 39.192 

2/1/2013 17:04:00 14.463 3.951 2.131 0.456 13.771 27.257 38.655 

2/1/2013 17:05:00 14.456 3.953 2.035 0.446 13.765 27.437 37.7 

2/1/2013 17:06:00 l4.465 3.948 2.002 0.413 13.765 27.313 37.85 

2/1/2013 17:07:00 14.484 3.936 1.936 0.411 13.766 27.313 38.072 

2/ 1/2013 17:08:00 14.481 3.936 1.945 0.402 13.766 27.277 38.207 

2/1/2013 17:09:00 14.484 3.933 1.937 0.408 13.766 27.251 38.323 

2/1/2013 17:10:00 14.486 3.932 1.914 0.417 13.768 27.261 38.214 

2/1/2013 17:11:00 14.451 3.945 2.05 0.4 13.766 27.303 38.34 

2/1/2013 17:12:00 14.456 3.944 2.072 0.399 13.766 27.301 38.282 

2/1/2013 17:13:00 13.174 3.467 2.173 0.441 2.83 8.648 75.893 

2/1/2013 17:14:00 0.381 0.223 0.156 3.299 0.05 0.987 138.384 

2/1/2013 17:15:00 0.199 0.198 -0.011'-! -4~3~8~3! 0.033 o 898! 138.99! 

2/1/ 2013 17:16:00 0.203 0.193 -0.017 4.409 1.906 0.824 136.615 

2/1/2013 17:17:00 2.868 1.768 -0.012 3.98 9.916 0.782 27.698 

2/1/2013 17:18:00 10.074 5.222 -0.013 0.221 9.965 0.729 -0.37 

2/ 1/ 2013 17 19 00'-!--;l';;'0711;-:3;-"""';'5-;2:':'44:;---;-0;-:00~8! -0.355'-! -9;;-9i;;6";'7-~0::-:6;';7~5! -0.389 

2/1/2013 17:20:00 10.159 5.221 -0.001 -0.387 5.473 14.622 3.82 

2/1/2013 17:21:00 3.069 0.932 3.697 -0.048 0.048 24.679 0.792 

2/1/2013 17:22:00 !--=0-= .. .2"'05"....-0"".""19"'4,--4"'. 7"'1"'5--'.,,0.-=1""3 --::.0 ."0"'25,--,2"'4-:.6"'8---""'0'"' .0"'5,,,7! 

2/ 1/ 2013 17:23:00 0.198 0.181 4.739 0.162 8.919 25.773 11.006 

2/ 1/ 2013 17:24:00 ..... --::..;0::;,.""1 _~0::;..1",4:...........;0;;,.4,;:1:,;1_....;0;.;.0;;;2;,.7 _....".1:,;.8:;;6:-.....;6;;,.2:,;0;;;6_...;2;,:2'=. 7.;:3.;,4 

2/1/2013 17:25:00! 0.097 0.136 -0.018 -0.037 0.024 0.196 0.041 

2/1/2013 17:26:00 7.099 3.898 2.698 1.364 5.042 9.719 10.431 

2/ 1/2013 17:27:00 10.107 5.251 4.759 4.361 9.987 24.501 127.253 

2/1/2013 17:28:00"! ....;1:,;0;;;1'"'14;--:;;5.~24~8:--4;;,. 7;,;6:,;5-.....;~4.;.;;4~3 -~9:;,99:;;4,-...".24;;,5:.;2;;;5-1:-:3:.;9;.;2;:;2;:,11 

2/1/2013 17:29:00 11.102 3.539 4.54 4.43 16.003 35.52 132.294 

2/1/2013 17:30:00 14.359 3.845 2.601 5.258 18.876 44.25 50.633 

2/1/2013 17:31:00 14.382 3.866 2.528 7.847 18.88 8.849 17.292 

2/1/2013 17:32:00 14.425 3.905 2.534 8.882 18.88 29.509 13.498 

TH( 

PPM 

1.207 

1.246 

1.354 

1.358 

1.344 

1.252 

1.393 

1.25 

1.305 

1.196 

1.327 

1.292 

1.333 

1.294 

1.042 

1.229 

1.186 

1.391 

1.408 

1.28 

1.366 

1.271 

1.218 

1.362 

1.36 

1.324 

1.48 

1.325 

1.376 

1.3 

1.255 

1.225 

1.25 

1.251 

1.366 

1.259 

1.241 

1.389 

0.802 

-0.011 

·0.01 CO bias 

-0.011 

-0.016 

-0.017 

-0.017 02/(02 bias 

0.118 

-0.017 

-0.017 NOx bias 

0.347 

1.406 

1.147 Direct Zero 

1.173 

1.187 

1.07 Direct Span 

0.93 

0.913 

0.852 

0.606 
~ ~ ~ w ~ ~ 

Date Time % % PPM PPM % PPM 

2/1/2013 17:33:00 14.458 3.899 2.528 9.311 18.88 48.34 

2/1/2013 17:34:00 14.445 3.906r!--:2;:;.5:;:2:::.4--=9:.::.4,;.33;.........,,18~.;;:88;:1~-4:-::8,:;3;;;5.,;,2! 

2/1/2013 17:35:00 14.477 3.893 2.157 9.418 18.8 15.494 

2/1/2013 17:36:00 14.482 3.893 1.992 9.356 18.779 0.517 

2/1/2013 17:37:00 14.485 3.892 1.98 9.308 18.778 0.438 

2/1/2013 17:38:00 14.473 3.893 2.024 9.273 18.779 0.411 

2/1/2013 17:39:00 14.483 3.892 2.1 9.23 18.779 0.378 

2/ 1/ 2013 17:40:00 14.477 3.892 2.171 9.182 18.779 0.363! 

2/1/2013 17:41:00 14.502 3.878 2.063 9.131 18.779 0.351 

2/1/2013 17:42:00 14.51 3.874 2.086 9.065 11.074 0.34 

2/1/2013 17:43:00 14.5l4 3.87 2.122 9.021 4.385 0.312 

2/1/2013 17:44:00 14.508 3.871 2.088 8.977 4.504 0.304 

2/1/2013 17:45:00 14.519 3.864 2.04 8.942 4.505 0.292 

2/1/2013 17:46:00 14.514 3.864 1.978 8.896 4.505 0.29 

2/1/2013 17:47:00 14.493 3.872 2.142 8.853 4.506 0.282 

2/1/2013 17:48:00 14.502 3.869 2.168 8.807 4.505 0.285 

2/1/2013 17:49:00 14.51 3.866 2.169 8.759 4.505 0.267 

2/1/2013 17:50:00 14.515 3.861 2.178 8.717 4.506 0.268 

2/1/2013 17:51:00 14.501 3.866 2.164 8.673 4.506 0.259 

2/1/2013 17:52:00 14.5 3.865 2.168 8.629 4.506 0.262 

2/1/2013 17:53:00 14.512 3.855 2.093 8.579 4.506 0.255 

2/1/2013 17:54:00 14.522 3.845 2.136 8.543 4.506 0.245 

2/1/2013 17:55:00 14.524 3.84 2.288 8.495 4.506 0.234 

2/1/2013 17:56:00 14.53 3.832 2.112 8.464 4.506 0.235 

2/1/2013 17:57:00 14.525 3.831 2.04 8.423 4.507 0.235 

2/1/2013 17:58:00 14.527 3.827 2.019 8.366 4.507 0.231 

2/1/2013 17:59:00 14.519 3.831 2.188 8.333 4.507 0.235 

2/1/2013 18:00:00 14.519 3.825 2.104 8.291 4.523 0.23 

2/ 1/2013 18:01:00 14.53 3.816 2.027 8.242 4.531 0.23 

2/1/2013 18:02:00 14.528 3.81 2.114 8.203 4.531 0.227 

2/1/2013 18:03:00 14.544 3.797 1.989 8.156 4.53 0.223 

2/1/2013 18:04:00 14.545 3.795 2.08 8.126 4.53 0.222 

2/1/2013 18:05:00 14.544 3.795 2.172 8.094 4.546 0.207 

2/1/2013 18:06:00 14.537 3.799 2.196 8.053 4.554 0.215 

2/1/2013 18:07:00 14.539 3.796 2.155 8.01 4.555 0.219 

2/1/2013 18:08:00 14.541 3.795 2.136 7.966 4.554 0.233 

2/1/2013 18:09:00 14.53 3.8 2.188 7.925 4.565 0.216 

2/1/2013 18:10:00 14.54 3.793 2.149 7.883 4.58 0.216 

2/1/2013 18:11:00 14.529 3.798 2.185 7.852 4.579 0.216 

2/1/2013 18:12:00 14.543 3.789 2.166 7.805 4.58 0.218 

2/1/2013 18:13:00 14.55 3.782 2.066 7.77 4.58 0.215 

2/1/2013 18:14:00 14.551 3.779 2.014 7.726 4.593 0.215 

2/1/2013 18:15:00 14.552 3.776 2.002 7.672 4.604 0.213 

2/1/2013 18:16:00 14.552 3.776 2.018 7.647 4.605 0.209 

2/1/2013 18:17:00 14.538 3.784 2.132 7.603 4.605 0.214 

2/1/2013 18:18:00 14.522 3.789 2.261 7.566 4.604 0.213 

2/1/2013 18:19:00 14.533 3.78 2.216 7.522 4.611 0.214 

2/1/2013 18:20:00 10.773 4.336 1.165 7.483 4.629 0.213 

2/1/2013 18 :21:00 !r--:1':::0~1.;,,66;--5~.~11~3! 0.022 7.446 4.629 0.218 

2/1/2013 18:22:00 10.165 5.12 0.012 7.408 4.629 0.206 

2/1/2013 18:23:00 10.145 5.11 0.008 7.376 4.649 0.199 

2/1/2013 18:24:00 1.763 0.572 3.685 7.355 4.654 0.201 

2/1/2013 18:25:00!..--=0::,.2;;:31;.....-:::,:0;;, .1! 4.754 7.304 4.654 0.198 

2/1/2013 18:26:00 0.164 0.063 4.759 7.268 4.666 0.202 

2/1/2013 18:27 :00!..--=0-:.0;:,99;.....-0;;.;;:03~2! 4.775 7.24 4.679 0.19 

2/1/2013 18:28:00 8.697 4.597 4.762 7.188 4.679 0.186 

2/1/2013 18:29:00!..--:1"0"".1",32"..........,5"."'11;,.,1! 2.917 7.152 4.679 0.189 

2/1/2013 18:30:00 16.571 8.538 2.155 7.118 4.691 0.165 

W 

PPM 

13.653 

14.801 

11.06 

10.274 

36.681 

229.991 

243.366 

243.287! 

192.146 

41.634 

7.484 

1.707 

0.762 

0.557 

0.546 

0.545 

0.547 

0.549 

0.524 

0.509 

0.424 

0.422 

0.399 

0.396 

0.398 

0.402 

0.404 

0.4 

0.396 

0.393 

0.395 

0.397 

0.392 

0.388 

0.391 

0.391 

0.39 

0.392 

0.39 

0.388 

0.392 

0.388 

0.394 

0.391 

0.393 

0.394 

0.392 

0.394 

0.395 

0.395 

0.399 

0.4 

0.379 

0.306 

0.245 

0.246 

0.248 

0.248 

THC 

PPM 

0.329 

0.329 NOx Mid, CO High, Inlet Direct High 

0.328 

0.328 

0.329 

0.338 

0.338 

0.337 CO-In Direct High 

0.336 

0.33 

0.329 

0.329 

0.328 

0.329 

0.329 

0.328 

0.328 

0.328 

0.329 

0.33 

0.329 

0.329 

0.33 

0.33 

0.33 

0.33 

0.33 

0.33 

0.329 

0.329 

0.329 

0.329 

0.328 

0.328 

0.329 

0.329 

0.329 

0.329 

0.33 

0.33 

0.33 

0.33 

0.331 

0.331 

0.331 

0.331 

0.331 

0.331 

0.331 02 bias 

0.331 

0.33 

0.331 

0.331 Zero bias 

0.33 

0.331 02/(02 Direct Zero 

0.331 

0.331 02/C02 Direct 5pan 

0.331 
0, co, 

Date Time % % 

2/1/2013 18 31:00IL.....:1:.:;9:.:.0~16;.._9~.;69;::J91 2/1/2013 18:31:30 11.533 9.704 

2/1/2013 18:31:40 3.961 9.709 

2/1/2013 18:31:50 3.872 9.71 

2/1/2013 18:32:00 3.828 9.704 

2/1/2013 18:32:10 3.825 9.706 

2/1/2013 18:32:20 3.814 9.703 

2/1/2013 18:32:30 3.8 9.704 

2/1/2013 18:32:40 3.8 9.701 

2/1/2013 18:32:50 3.807 9.699 

2/1/2013 18:33:00 10.657 9.7 

2/1/2013 18:33:10 14.606 9.699 

2/1/2013 18:33:20 14.97 9.698 

2/1/2013 18:33:30 15.041 9.698 

2/1/2013 18:33:40 15.062 9.695 

2/1/2013 18:33:501 15.0661 9.694 

2/1/2013 18:34:00 14.563 9.694 

2/1/2013 18:34:10 11.764 9.694 

2/1/2013 18:34:20 11.319 9.694 

2/1/2013 18:34:30 11.256 9.689 

2/1/2013 18:34:401 11.2351 9.689 

2/1/2013 18:34:50 11.227 9.688 

2/1/2013 18:35:00 11.226 9.685 

2/1/2013 18:35:10 10.264 9.683 

2/1/2013 18:35:20 9.467 9.681 

2/1/2013 18:35:30 9.394 9.68 

2/1/2013 18:35:40 9.37 9.677 

2/1/2013 18:35:501"-9~3;;:;6;;'91 9.679 

2/1/2013 18:36:00 8.915 9.676 

2/1/2013 18:36:10 7.681 9.675 

2/1/2013 18:36:20 7.529 9.671 

2/1/2013 18:36:30.LI_-:7~.5;711 9.669 

2/1/2013 18:36:40 6.74 9.671 

2/1/2013 18:36:50 4.208 9.669 

2/1/2013 18:37:00 3.87 9.67 

2/1/2013 18:37:10 3.825 9.668 

2/1/2013 18:37:201 3.8011 9.666 

2/1/2013 18:37:30 5.544 9.664 

2/1/2013 18:37:40 9.544 9.661 

2/1/2013 18:37:50 10.004 9.663 

2/1/2013 18:38:00 10.082 9.661 

2/1/2013 18:38:10 10.104 9.661 

2/1/2013 18:38:201 10.1161 9.659 

2/1/2013 18:38:30 10.181 9.657 

2/1/2013 18:38:40 13.46 9.655 

2/1/2013 18:38:50 14.927 9.651 

2/1/2013 18:39:00 15.052 9.649 

2/1/2013 18:39:10 15.078 9.645 

2/1/2013 18:39:20 15.09 9.643 

2/1/2013 18:39:30"1 -1~5':;;.0;;'91 9.644 

2/1/2013 18:39:40 14.028 9.64 

2/1/ 2013 18:39:50 11.588 9.638 

2/1/2013 18:40:00 11.306 9.636 

2/1/2013 18:40:10 11.255 9.634 

2/1/2013 18:40:20 11.248 9.633 

2/1/2013 18:40:301 11.2381 9.632 

2/1/2013 18:40:40 10.727 9.627 

2/1/2013 18:40:50 9.574 9.625 

NO, 

PPM 

2.163 

1.452 

0.09 

0.082 

0.052 

0.054 

0.057 

0.052 

0.05 

0.043 

0.042 

0.043 

0.045 

0.043 

0.043 

0.038 

0.045 

0.054 

0.049 

0.043 

0.047 

0.041 

0.037 

0.056 

0.053 

0.042 

0.042 

0.04 

0.043 

0.037 

0.045 

0.059 

0.072 

0.067 

0.076 

0.083 

0.192 

0.299 

0.217 

0.167 

0.156 

0.162 

0.127 

0.108 

0.094 

0.106 

0.078 

0.07 

0.067 

0.063 

0.059 

0.063 

0.058 

0.05 

0.051 

0.057 

0.056 

0.062 

co 

PPM 

7.072 

7.053 

7.013 

7.033 

7.037 

7.041 

7.01 

7.002 

6.992 

6.976 

7.002 

6.98 

6.995 

6.972 

6.969 

6.958 

6.948 

6.965 

6.939 

6.944 

6.939 

6.897 

6.922 

6.911 

6.902 

6.905 

6.906 

6.891 

6.866 

6.877 

6.876 

6.869 

6.881 

6.851 

6.844 

6.843 

6.812 

6.839 

6.823 

6.844 

6.817 

6.813 

6.808 

6.794 

6.781 

6.813 

6.786 

6.771 

6.771 

6.735 

6.741 

6.756 

6.763 

6.749 

6.732 

6.723 

6.702 

6.705 

0, 

% 

4.703 

4.704 

4.703 

4.703 

4.704 

4.704 

4.704 

4.704 

4.704 

4.704 

4.72 

4.729 

4.728 

4.728 

4.728 

4.728 

4.728 

4.728 

4.728 

4.729 

4.728 

4.729 

4.728 

4.728 

4.729 

4.729 

4.728 

4.728 

4.728 

4.728 

4.728 

4.739 

4.752 

4.753 

4.753 

4.753 

4.753 

4.753 

4.753 

4.753 

4.752 

4.752 

4.753 

4.753 

4.752 

4.752 

4.752 

4.752 

4.753 

4.753 

4.753 

4.753 

4.754 

4.753 

4.753 

4.753 

4.753 

4.752 

NO, 

PPM 

0.17 

0.162 

0.157 

0.154 

0.156 

0.155 

0.163 

0.165 

0.157 

0.172 

0.159 

0.156 

0.156 

0.169 

0.156 

0.159 

0.156 

0.159 

0.166 

0.159 

0.166 

0.139 

0.139 

0.17 

0.168 

0.17 

0.17 

0.17 

0.166 

0.159 

0.172 

0.17 

0.172 

0.18 

0.175 

0.164 

0.17 

0.17 

0.187 

0.176 

0.187 

0.173 

0.17 

0.17 

0.169 

0.166 

0.156 

0.165 

0.169 

0.169 

0.156 

0.155 

0.154 

0.149 

0.163 

0.151 

0.152 

0.156 

co 

PPM 

0.206 

0.232 

0.246 

0.251 

0.249 

0.248 

0.146 

0.201 

0.249 

0.248 

0.246 

0.141 

0.197 

0.245 

0.248 

0.25 

0.145 

0.199 

0.143 

0.091 

0.193 

0.248 

0.246 

0.249 

0.253 

0.25 

0.248 

0.143 

0.094 

0.2 

0.25 

0.246 

0.244 

0.248 

0.254 

0.25 

0.249 

0.351 

0.396 

0.501 

0.548 

0.649 

0.693 

0.593 

0.545 

0.546 

0.552 

0.553 

0.558 

0.556 

0.449 

0.402 

0.4 

0.395 

0.397 

0.398 

0.293 

0.35 

TH( 

PPM 

0.331 02/(02 Direct High 

0.331 

0.331 

0.331 

0.331 

0.332 

0.332 

0.331 

0.331 

0.331 

0.332 

0.33 

0.331 

0.33 

0.33 

0.331 

0.33 

0.331 

0.331 

0.33 

0.331 

0.331 

0.33 

0.33 

0.331 

0.33 

0.33 

0.33 

0.33 

0.33 

0.331 

0.331 

0.331 

0.331 

0.331 

0.331 

0.331 

0.33 

0.33 

0.33 

0.331 

0.33 

0.33 Mid 

0.331 

0.331 

0.331 

0.331 

0.331 

0.332 

0.331 

0.331 

0.331 

0.332 

0.332 

0.331 

0.331 

0.331 

0.331 

80% 

60% 

50% 

40% 

20% 

80% 

60% 
0, 

Oate Time % 

2/1/2013 18:41:00 9.408 

2/1/2013 18:41:10 9.385 

2/1/2013 18:41:20Ir -"i:9~.3:':171 

2/1/2013 18:41:30 8.857 

2/1/2013 18:41:40 7.671 

2/1/2013 18:41:50 7.53 

2/1/2013 18:42:00 7.51 

2/1/2013 18:42:10

r

l -7~.5~0:::t91 

2/1/2013 18:42:20 6.738 

2/1/2013 18:42:30 4.212 

2/1/2013 18:42:40 3.874 

2/1/2013 18:42:50 3.823 

2/1/2013 18:43:oo

r

l --";3:-;;.8"'0:':131 

2/1/2013 18:43:10 4.181 

2/1/2013 18:43:20 8.922 

2/1/2013 18:43:30 9.934 

2/1/2013 18:43:40 10.068 

2/1/2013 18:43:501 10.0911 

2/1/2013 18:44:00 10.101 

2/1/2013 18:44:10 11.91 

2/1/2013 18:44:20 14.758 

2/1/2013 18:44:30 15.005 

2/1/2013 18:44:40 15.04 

2/1/2013 18:44:50

r

l """""15;;;.0;;5""31 

2/1/2013 18:45:00 14.122 

2/1/2013 18:45:10 11.599 

2/1/2013 18:45:20 11.292 

2/1/2013 18:45:301 11.2361 

2/1/2013 18:45:40 11.169 

2/1/2013 18:45:50 9.834 

2/1/2013 18:46:00 9.422 

2/1/2013 18:46:10 9.374 

2/1/2013 18:46:201 

9.3691 

2/1/2013 18:46:30 8.912 

2/1/2013 18:46:40 7.675 

2/1/2013 18:46:50 7.523 

2/1/2013 18:47:001 7.4991 

2/1/2013 18:47:10 6.488 

2/1/2013 18:47:20 4.145 

2/1/2013 18:47:30 3.861 

2/1/2013 18:47:40 3.82 

2/1/2013 18:47:501.--:3:::.8"'0:;,21 

2/1/2013 18:48:00 3.806 

2/1/2013 18:48:10 7.892 

2/1/2013 18:48:20 9.841 

2/1/2013 18:48:30 10.041 

2/1/2013 18:48:40 10.087 

2/1/2013 18:48:501 10.0911 

CO, 

% 

9.625 

9.626 

9.622 

9.62 

9.616 

9.612 

9.613 

9.607 9.607 

9.604 

9.603 

9.599 

9.595 

9.592 

9.59 

9.588 

9.588 

9.586 

9.581 9.579 

9.576 

9.574 

9.571 

9.568 

9.565 

9.563 9.563 

9.557 

9.556 

9.551 

9.547 

9.545 9.543 

9.542 

9.539 

9.534 9.532 

9.531 

9.524 

9.522 

9.523 

9.519 

9.513 

9.513 

9.506 9.506 

9.502 

9.502 

NO, 

PPM 

0.065 

0.054 0.055 0.05 

0.043 

0.041 0.046 0.04 

0.043 

0.049 

0.047 

0.043 

0.044 0.045 

0.044 

0.059 0.047 

0.048 

0.039 

0.048 

0.044 

0.051 

0.057 

0.05 

0.042 

0.044 

0.047 

0.043 

0.047 

0.048 

0.043 

0.037 0.044 

0.044 

0.052 

0.039 

0.044 

0.038 

0.039 

0.037 

0.039 

0.043 

0.048 

0.D35 0.038 

0.043 

0.034 

0.036 

CO 

PPM 

6.713 

6.699 

6.717 6.69 

6.703 

6.699 6.677 6.669 6.673 

6.658 6.673 6.642 

6.599 

6.623 

6.666 6.636 

6.639 

6.617 

6.618 6.577 

6.587 

6.591 

6.589 

6.622 6.605 6.586 6.558 6.539 6.577 

6.53 

6.546 

6.524 

6.517 

6.525 

6.522 6.496 6.526 6.519 

6.493 

6.472 

6.445 

6.487 

6.505 6.469 

6.469 

6.464 

6.452 

6.422 

0, 

% 

4.755 

4.774 

4.777 4.777 4.778 

4.777 

4.777 

4.778 4.778 

4.778 4.777 4.777 4.778 

4.777 

4.777 4.778 

4.778 

4.777 

4.777 4.777 4.778 4.778 

4.777 

4.777 

4.778 4.777 4.777 

4.777 4.777 

4.789 

4.801 4.802 4.801 4.802 

4.802 

4.802 4.802 4.801 

4.8 

4.801 

4.8 

4.801 

4.801 

4.802 4.802 

4.801 

4.801 4.801 

NO, 

PPM 0.155 

0.151 

0.153 0.143 

0.154 0.147 0.147 0.14 0.146 

0.161 

0.14 0.14 0.14 

0.14 0.14 0.14 0.14 

0.152 

0.158 0.138 

0.14 

0.14 

0.148 0.14 0.142 

0.14 

0.147 0.147 

0.14 

0.14 

0.14 

0.134 0.14 

0.14 

0.152 

0.143 

0.151 0.141 0.14 0.14 0.14 0.14 

0.138 0.13 0.141 0.138 

0.124 0.131 

CO 

PPM 0.395 0.291 

0.349 0.396 

0.399 

0.398 0.398 0.287 

0.344 

0.289 0.244 0.246 0.243 

0.239 0.244 

0.244 0.244 

0.245 

0.245 

0.245 0.247 0.244 

0.249 0.247 0.25 

0.248 

0.243 0.248 

0.247 

0.247 

0.244 0.25 0.251 

0.243 

0.246 0.245 0.244 0.242 

0.239 0.241 

0.236 

0.243 

0.241 

0.247 0.25 0.244 

0.242 

0.245 

THC 

PPM 

0.331 

0.331 

0.331 0.331 0.329 0.33 

0.33 0.33 0.33 

0.331 

0.33 0.33 

0.33 

0.331 

0.331 

0.33 

0.329 

0.33 Mid 

0.33 0.33 0.33 

0.33 

0.331 

0.331 0.33 

0.331 0.331 0.331 

0.331 

0.331 

0.332 0.331 

0.331 

0.331 

0.331 

0.331 

0.331 

0.331 

0.333 

0.333 

0.333 

0.332 

0.332 0.33 

0.33 

0.33 

0.331 

0.33 Mid 

50% 40% 

20% 

80% 

60% 

50% 

40% 

20% 
Appendix C.3 Ammonia Data by SCAQMD Method 207.1 

R0410673 C-7 
AMMONIA TEST RESULTS SUMMARY 

Client Gemma Parameter 

Location CPV Sentinel Fuel 

Unit 2 Data By 

Test Number CPV Sentine!~2· NH3-55-1 CPV Sentine ~2 NH3-56-2 

Reference Temperature, F 60 60 

Test Date 21112013 21112013 

Test Method SCAQMD 207.1 SCAQMD 207.1 

Sample Train 9-P&M 9-P&M 

Meter Calibration Factor 0,992 0,992 

Stack Area (sq ft) 143.14 143.14 

Sample Time (Min) 60 60 

Barometric Pressure {in Hg}_ 29.69 29.69 

Start Time 14;20 15:53 

Stop Time 15:35 17:09 

Meter Volume (act) 48,058 44.351 

Meter Temperature (F) 80.7 78.4 

Meter Pressure (iwg) 1,83 1.60 

liquid Volume (ml) 99.3 96.0 

Stack 02 (%) 14,38 14,36 

Stack NOx (ppm) @ 15% 02 1.99 2.05 

Unit Load MW 55 56 

Fuel Flow Rate, hscfh 5,361 5,391 

Standard Sample Volume (SCF) 45.700 42.332 

Moisture Fraction 0.092 0.095 

Stack Flow Rate (dscfm, 60 of) 282,277 278,356 

Stack Flow Rate (dscfm 70 of) nla nfa 

Gas Constant (ft-lbfllb-mole-R) 1545.33 1545.33 

Standard Pressure (lbf/ft2) 2116.224 2116.224 

Molecular Weight NH3 (Ibllb-mole) 17 17 

Specific Molar Volume (ft3Itb-mole) 379.50 379.50 

Mass Conversion (lb/ug) 2.20E-09 2.20E-09 

02 Correction Factor (%) 15 15 

Mass NH3 (ug/sample) 669.90 769.60 

Mass NH3 (mg) 0.670 0.770 

Mass NH3 (Ib) 1.48E-Q6 1,70E-06 

PPM NH3 (flue gas) 0,7 0.9 

PPM NH3 @ 02 Correction 0,7 O,B 

Ib/hr 0.55 0,67 

Ib/MMscf fuel 1,02 1,24 

NH3 EQUATIONS; 

ppm NH3 = (mass NH3* Gas Const * Ref Temp * 106 )/(Sample vol. • Press * MW) 

ppm NH3 @ 02 correction = ppm * (20.9-02 Corr)/(20.9-%02) 

NH3 

natural gas 

AA, SP, SS, JM 

Averaae limit 

14.37 

2.02 

O.B 

0.73 5 

0.61 

1.1310 
WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: !';1\::;.tlN) ." AMBIENT TEMPERATURE: ,3- LOCATION: S "" lAY p'V- 5 ;;::cl' ?9.tc,;J'I/S~2 BAROMETRIC PRESSURE-: 2J~"--;.b-;"'------------

DATE: '211/'3 ASSUMED MOISTURE: "\°1,, 

RUN NO: ~ - 2> S 1'1"- - Alif~ - 50-I PITOT TUBE COEFF, C-p': tc'-:co-". '\~~;;----- ---

OPERATOR: '':> ~"'"" PROBE ID NO/MATERIAL: ott oo'i? 

METER BOX NO: "\ ~""- PROBE LENGTH:_.tch_" _ _ --,.,-___ ____ _ 

METER t.H@: \. ~"'1 NOZZLE ID NOI MATERIAL: 1'1(+ 

METER Yd: o. '\otL NOZZLE DIAMETER: rv(4 STACK AREA, FT' : lin <l,,\ FILTER NOITYPE: -1'1-'-"','=-1'<'-------- ---

TRAVERSE POINTS, MIN/POINT: '12\I?- PRE·TEST LEAK RATE:: L.<j.&i?c;FM@ t:;;: in. Hg. 

t.H= ~ X t.P: ./ /' POST·TEST LEAK RATE: : L.O.cil? CFM@ I '5 in. Hg. 

Probe Condition, pre/post testJ

, · PITOT LEAK CHECK · PRE: ,/ POST:~ 

Silica Gel Expanded, YIN: ~ CHAIN OF CUSTODY: SAMPLE CUSTODIAN-,"={>. _ _ _ 

Filter Condition after Test Nt\" SAMPLER=')"' ... -,-,~ __ Check Weight Z SAMPLE CUSTODIAN l'<AImp. # Contents Post·Test· Pre·Test = Difference 

.I- \i\Jll ~<f '80(, l{"'-~=S2-'-.7L __ _ 

;;A d , \ II; Il'Zsoj t:J/6 g-- (-.k3, Z-=-. _ 

J. C ,...,?!:, 5f'3. '7 5e>2-. > , - -

.!1. S'G- C/lc-, 'Y2ciJ,Jo _ _ 

L..A - 1'0 c) 

Total: _____________ _ 

Meter t.P t.H Stack Probe Filter Imp. Out Meter Tsmp, of Vacuum 0, P. static 

Point Time Volume, ft' in. H,O in, H,O Temp, of \, Temp, of Temp, of Temp, of In Out in, Hg, % in, H,O 

5 3 1'-12..'" '12.V)~ lyW O.\pl ,/..:l:2-') /'14 ()ItA- tJt i'r {,.'-t ",0., '77 .1 ,<C. .a I~., .. 2-L 

2- I '{ '2 '5" ~ O ,t..6 , 1:;' -.l [ \ 

1 1'-/;"0> 2. ,?:1 ;,2. -n.;l , \ 

CfVV ('fO q~.">"-- II C)"S 1,).. 

It '3 1,\3"1 tI~b.712- I'-It< &.L"O t,:, lib bJ.., 0-{ 'I~ h-,.' 

'2- l'i't'f q 0,'5'\ '1'.2> 

1 V-!'1'9 11 D .C",3 1l4> 

lire", 0 VttS'l. ~ q 1/P/ z. I V .ld., l15 

,,;3 \<;[-) 1 C\~1 812.- 1--Ie-O d"D V'I I 'l l Gl ,3, ,6i C,·.D 

'2.- 1<;0&. ~ ,p.rn"> .'70 

\ ' '; i 1 '2 cf) ·1.2.. l,b 

r't/rv(/ \ )1 ~ 'I'>'i.02.6 I b . 'O) 171 

vJ ') \ <;Zu qS-q .b '2" L\ S I~ ,1 ) :-j 1 1 '-f i.:H '32-"~ ') <> 

1.. i')7-> " '6 D "7'1 ' 

\ 15'1'''' 1- D ."1 ", \>, 

~"'O I,),) '172.1'1{; \ f) . "6.' '1'1 '1 

~ \ , AveraQe: I:> \1<" 

Comments: ____________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page .-L. of 1- D8834049 

Master Document 8torage\Forms\Datasheets\Field Datasheets 
s 

.,; 

fI 

vJ 

IW 

Della~ _ _ _ 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: tJ,.P./Y"" /h-~ 

LOCATION::1:/ 4"1-"< d (C'" - f .2.. 

DATE: :J -- ) 1:3 

RUN NO: 0 ' :J.JS -A' 93 - 5"0-· '1' 

OPERATOR: 6.5 METERBOX7N~0 :~Sn1 ~~~----

METER t.H@: \ . 3'lQ METER Yd: .---"-"""-'-::Q'--,"<1"'i"')"'---

STACK AREA, FT2: 143.1 '+ 

TRAVERSE POINT"'S", '"'M~'N';';/;:!-PO='N"'T:- : - 5=/'(2::-.• -

t.H= /V!>: X t.P: 

Probe Condition, prelpost test v',./' 

Silica Gel Expanded, YIN : i\J 

Filter Condition after T est-I N:-I:~2"- Check Weight _ __ -'/'-_ _ ___ _ 

Meter t.P 

Point Time Volume, ft' in. H,O 

..4/ ' 1'5'> <, ,,\1 ;-:; i1 i 4' ) 

·2 \ C, oJ' 3 &v'&;? 

I i003 2. &..,9vf) 

;:'1'1" Ibo15 Q, X'l; I, \ I ~>'IO 

t>/fJ.-" \ (,,{ J- " n.ni +,..-to-"(; "t 

1..- IlIl 30.[g'l 

I \ (, 2.'L A t> ! "00 

i'O rvC! \\"J,.l 31i·D\1o \ o Jb8 

?'? \ t,,'t '1'14 ,"It, '-\' '" C • 5'\ 

2.- I b":>1 3 /), "'S 

1 lu'lf L.. e .tp'?> 

(i, vv Ib'I'1 I 00"\. \ 2;;- \ t> ,L,l2 

1"''- ~ \ 1o'5l\. rD <to \ \/;-- I 't "'0.5,\ 

'}.. )b)'\ ->: e ... o 

1 nOli ., ~ , 1,,"1 

!:rvP_ i1.D"! . 0 1"1/,2."'1 , 0 .1"1 

Average: 

~ 

AMBIENT TEMPERATURE: J ~ BAROMETRIC PRESSURE:--;2""" -d7

,,' "8---''=------- ASSUMED MOISTURE: '1 ' Ie> 

PITOT TUBE COEFF, C-P-+: O-'-"'.q-=q-:-· - - - - - ----

PROBE ID NO/MATERIAL: .. :ll§~Q""o,-,g,,--_ _ _ _ _ _ _ _ 

PROBE LENGTH: 6 ' 

NOZZLE ID NOI M·:-:A-=T=E""R:-"A:;>" L-: ·~"'7r.,,----- --

NOZZLE DIAMETER:_--,'CI\'fI Ic-,"' _ _ _ ____ __ _ 

FILTER NOITYPE: .<v/h 

PRE-TEST LEAK RATE: : La .DO"/' CFM@ \ <; in. Hg. 

POST-TEST LEAK RATE: "-' 0.)'2 CFM@ I i in. Hg. 

PITOT LEAK CHECK - PRE: ......- POST. , __ 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN,-=o,"'(),'---__ 

SAMPLER ,)""- SAMPLEC~U~S D~IA~N~A~A --

t.H Stack Probe Filter Imp. Out 

in. H,O Temp, OF Temp, OF Temp, OF Temp, OF 

\ . 8 """\'DC:> A;I? Iv/rv bo ... ""...,... 

1'0 \ 

" 'c)D 

I ,'b ,,'1 ""2- 'l'OO 

'\9>.() 

'1.0 "- I " L{ '1''', S") 

'l'q. 'b -n y 

~ 

l- tt '1'6'" ,,><= 

< Q,I 

VO \ 

"'6 \ 

,. II I 

.. - - - _ .- -- .-'-- --

Imp. # Contents Post-Test - Pre-Test = Difference 

__ I 

1:-

3 

--.!i. 

(P , I/'; H '6,t~ "7tl J JO;(,l2fL116 I,,!... __ _ 

_ _ '_' _ 70(;, Fe 765 __ 

/"' "\-

6G~ 

~1, Y 6,5€-'i __ 

qb (-'! '15<f3 _ _ 

I, ~ it! R i',(' 'J-i' -- (00 

Total: _ _ _ ________ __ _ 

Meter Temp, OF Vacuum 0 , P. static 

In Out in. Hg. % in. H,O 

)10 1& <= n ·) -r 2-, , 

'87 1 .4 6' n 

~O 1 25 ,,0 

'80 1S '>.0 

--

Comments: ____________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page __ of _ _ 

DS834049 

Master Document Storage\FormslDatasheetslField Datasheets 
AMMONIA ELECTRODE CALIBRATION CURVE 

"ample "oom 

NH, concentration log NH, concentration Electrode potential Temperature Temperature 

(~g NH,I ml as N) (mV) (C) (C) 

1 0.000 89.4 21 21 

5 0.699 53.4 21 21 

20 1.301 18.6 21 21 

100 2.000 -21.7 21 21 

Ammonia Electrode Calibration Curve y = -55.7371x + 90.6621 

210512013 R' = 0.9992 

100.0 

;;- 80.0 

Eo; 60.0 

., 

.: 

.$ 

0 

40.0 

0.. 

.. 20.0 "C 

0 

~ 

ti 0.0 

~OO .. 

jjj -20.B( 00 0.500 1.000 1.500 

-40.0 -

logarithm of the concentration of ammonia (l1g NH,I ml as N) 

slope 

y-intercept 

Concentration 

(~g NH,I ml as N) 

1 

5 

20 

100 

Calculation: 

-55.7371 

90.6621 

Value LR line 

1.0535 

4.6616 

19.6288 

103.7362 

Regression Line: P=M"log(l1g of NH,t ml as N)+B 

Difference 

0.0535 

-0.3384 

-0.3712 

3.7362 

Measured Concentration of Ammonia (C) in ~g 1 ml NH, as N: C=10(P.BVM 

where P = electrode potential, M= slope (must be -57±3) and B= intercept 

% Difference 

5.3522 

-6.7684 

-1 .8562 

3.7362 

All standards were prepared in 0.04N H2S04 and allowed to equilibrate to room temperature. 

2. 00 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS CALCULATION 

ClienU Location: 

Sample Location: 

District Method: 

Sample Date: 

Analysis Date; 

Analyst's Initials: 

Calibration Curve: 

R' 

Sample 

GEMMA 

Sentinel Unit 2 50% 

SCAQMO 207.1 

211/2013 

215/2013 

RF 

y= -55.7371 x+ 90.6621 

0.9992 

P Cone. 

mV )..19 NH3/ml as N 

26 ug NH3I ml as N 9.9 

repeal 26 ug NH3Iml as N 10 

1·NH3S0% 63.4 

repeal 1- NH3 50% 63.6 

2-NH3 50% 64.5 

repeat 2- NH3 50% 65.4 

spike 2-NH3 50% 17.2 

repeat spike 17.4 

Reagent Blank 151 .0 

repeat ReaQent Blank 151.4 

Field Blank 115.4 

repeat Field Blank 114.9 

0 1 H20 Blank 135.6 

Repeal 01 H20 Blank 136.1 

26 NH3/ml as N 10.1 

repeal 26 ug NH3Iml as N 9.9 

Notes: 

Measured Concentration of Ammonia (e) in f.l9 NH3 1 ml as N 

C=101P-S)lM 

P = electrode potential (mV), M=slope and B=intercept 

26.116 

26.002 

1.350 

1.339 

1.290 

1.243 

20.797 

20.626 

0.063 

0.061 

0.360 

0.367 

0.156 

0.153 

27.667 

26.116 

Average Measured Ammonia Concentration (Cavg) = (C1 + C2)/2 

where C1, C2 results from duplicate analyses (Jl9 NH3/ml as N) 

Cavg (~g NH,/ml as NH3) = Cavg (~g NH31 ml as N) ·17.03/14.01 

J.19 NH3 I sample = Cavg (J..Ig NH3/ml as NH3) .. TV 

Used 100 ml of samples and standards with 2 mllSA and constant stirring rate. 

Solution turned blue and remained blue with ISA. 

CavgasN 

26.060 

1.344 

1.266 

20.712 

0.0620 

0.3636 

0.1546 

26.002 

Maximum samples {including blanks} between 28 ug/ml check standard is 5 samples and a spike 

analyzed in duplicate. 

TV C avg as NH3 g NH,I 

(ml) sample 

NA 34.1 09 NA 

410 1.634 669.960 

500 1.539 769.669 

NA 25.177 NA 

NA 0.100 NA 

350 0.442 NA 

NA 0.166 NA 

NA 34.036 NA 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS QUALITY CONTROL 

ClienV Location: 

Sample Location: 

District Method: 

Sample Date: 

Analysis Date: 

Analyst's Initials: 

Sample 

28 ug NH3 1 ml as N 

repeat 28 uq NH3/ml as N 

1-NH350% 

reo eat 1- NH3 50% 

2-NH3 50% 

repeat 2- NH3 50% 

spike 2-NH3 50% 

repeat so ike 

Reagent Blank 

reoeat Reaoent Blank 

Field Blank 

repeat Field Blank 

01 H20 Blank 

Repeat 0 1 H20 Blank 

28 NH3/ml as N 

repeat 28 Uq NH3/ml as N 

Notes: 

GEMMA 

Sentinel Unit 2 50% 

SCAQMD 207.1 

2/1/2013 

2/5/2013 

RF 

% recovery 

NA 

NA 

NA 

101 .24 

NA 

NA 

NA 

NA 

spike: 100 ml sample + 2 ml (1000 ~g NH31 ml as N) 

Matrix Spike Percent Recovery (%R) 

%R = (C spike'O.104 - Csample'O. 1 02)/2 '100 

Cspike = average result of matrix spike (~g NH,I ml as N) 

RPD 

% 

0.41 

0.83 

3.72 

0.83 

1.65 

-2.07 

2.07 

-0.83 

RPA 

% 

0.214 

NA 

NA 

NA 

NA 

NA 

NA 

0.008 

Relative Percent Difference (RPD) = (C1-C2)1 Cavg '100 (must be 5% or less) 

Relative Percent Accuracy (RPA) (must be 10% or less) 

RPA = (Cavg-theoretical value of standard)1 theoretical value of standard' 100 
88118/1 

IW ....,uy ., Ince~ 

AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS 

Project #: District Method: SCAQMD 207.1 Sample Date: 2/ i /13 

Client/Location: G £ M M,4 Calibration Date: 2 ;913 Analysis Date: 7./4 / 13 

Sample Location: .s..nL;~ t./ u 2. Calibration Curve: It' -~. 7;/ X ./Y6.U Z I Analyst's Initials: R l' 

Test#'s: 5D% R': 0.9972.. ' 

Sample Electrode TV Cone. Cavg fig NH,I Commentsl Temp/pH 

Potential (ml) fig NH,- (fig NH, sample 

(mV) N/ml - N 1 mil 

Standard Check: Percent Recovery: 

28 ~g NH,Iml 

'1'7 2f·I/~ 

Repeat 28 /0·0 2f.cxn. J./i'.oto 

/- 1./1/, '.5'0% fs·'/ 1350 0 /NJet.t /-NJI, - S/./'/n ~J.t ~Ib 1.]19 13'/'1 t(7.Y IJ/J.l. 2- /"-"21<::.. ,~ 

2 - N IIr st.Plp H ·s I. '- 90 

l/{eAed 2,-)/(/,-50% 55·"1 SOD / . lIt] I·U? 7C9.C Ill//'" 2. ,=2.\0,-

t:.f.l)/(t. 2. .NI/,: so"l'o 1'7.2. 2e>, J'i7-

Re Mt;i S;t'J.(L J'f."1 2 D . (,2(- }'0.112 ID. u..; /6/% 

Re~q.e..,i n!r,y..K /$/,0 b.Of1 f 

Rl.t,. I: R. ~ I Sf. t.f Cu, & I O,Of2D 

FIe. Id P.1w. k' {I::', If 6·3,0 AI/so/vi/Dr! S 

l<t./JR6t f/<. /l1,{,c, (? .,3(; '7 6.]r...:(, LedecJ c.1:: 

fJl /./, (-, f?1v.-. t /35.(- D./5(, 2\ 0 c. 

Re..JJe.d /DII/Lo oS! K. /!J,. { 6./~ (') .151ft 

2,[·/vW .... /6,( zr.~J7 

RJl./'€4 C 2PJ///, 9.'7 2~, Iff 2&'.002.. , 

Notes: Total volume of samples and standards used: 100 ml 

Volume of pH adjusting ISA used in ml: 2 ml 

Absorbing solution: 0.1 N H2S04 

Calculations: Conc. (fig NH, - N 1 ml) = 10 (P·B)IM 

P = electrode potential, B = y·intercept and M = slope 

Cavg = average result of duplicate analyses (fig NH, - N 1 ml) = (C1+C2)/2 

fig NH,I sample = Cavg* 17.03/14.01 * TV 

mg 1 sample = fig Isample .,. 1000 

ppm NH, = mg NH,Isample x 1Nmstd x 1/454000 x SV/17 x 10· 

Del/ab.. 

---- - DS834059 

Date of last revision 12/5/2008 Master Document Storage\Forms\Datasheets\Lab Forms 
AMMONIA TEST RESULTS SUMMARY 

Client Gemma Parameter 

location CPV Sentinel Fuel 

Unit 2 Data By 

Test Number CPV Sentlnel-2-NH3-80-1 CPV Sentinel-2-NH3-80-2 

Reference Temperature, F 60 60 

Test Date 21112013 21112013 

Test Method SCAQMD 207.1 SCAQMD 207.1 

Sample Train 9·P&M 9·P&M 

Meter Calibration Factor 0.992 0.992 

Stack Area (sq ttl 143.1 4 143.14 

Sample Time (Min) 60 60 

Barometric Pressure (in Hg) 29.69 29.69 

Start Time 9:10 11:05 

Stop Time 10:34 12:15 

Meter Volume (act) 44.244 48.914 

Meter Temperature (F) 78.8 82.7 

Meter Pressure (iwg) 1.90 2.10 

Liquid Volume (ml) 92.6 111.8 

Stack 02 (%) 13.47 13.32 

Stack NOx (ppm) @ 15% 02 2.27 2.16 

Unit load MW 80 80 

Fuel Flow Rate, hscfh 6,912 6,936 

Standard Sample Volume (SCF) 42.226 46.369 

Moisture Fraction 0.093 0.101 

Stack Flow Rate (dscfm, 60 of) 306,797 301,392 

Stack Flow Rate idscfm, 70 oFi nJa nJa 

Gas Constant (ft-Ibfllb-mole-R) 1545.33 1545.33 

Standard Pressure (lbflft2) 2116.224 2116.224 

Molecular Weight NH3 (Ibllb-mole) 17 17 

Specific Molar Volume (ft3/1b-mole) 379.50 379.50 

Mass Conversion (Ib/ug) 2.20E·09 2.20E·09 

02 Correction Factor (%) 15 15 

Mass NH3 (ug/sample) 1029.45 1217.46 

Mass NH3 (mg) 1.029 1.217 

Mass NH3 (Ib) 2.27E·06 2.68E-06 

PPM NH3 (flue gas) 1.2 1.3 

PPM NH3 @ 02 Correction 1.0 1,0 

Iblhr 0.99 1.05 

Ib/MMscf fuel 1.43 1.51 

NH3 EQUATIONS: 

ppm NH3 = (mass NH3" Gas Canst" Ref Temp .. 106 )/(Sample vol." Press" MW) 

ppm NH3 @02correction=ppm·(20.9-02 Corr)/(20.9-%02) 

NH3 

natural gas 

M, SP, 55, JM 

A\ler~ge Limit 

13.39 

2.22 

1.2 

1.0 5 

1.02 

1.4698 
"'a..., Oe//atJ. _ _ 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: L:: "V,c..-

LOCATION: ;; ,. {" ,··-I r IJ.,.,ff aDATE: "'-/- 13 

RUN NO: 5-.)./5 - )/1·13 -7'5 - 1 

OPERA TOR ~:5",:s'--r,---;;---;-____ _ 

METER BOX NO: 5 f'><1' 

METER t.H@:.----:.! '-.S ' 8L!~---'~-=-7'7":----- METER Yd: " . I{"i 2.-

STACK AREA, FT': 1~\.i4 , 

TRAVERSE POINTS, MIN/POINT: Flt :l... t. ~ ,..1/", X t.P: 

probecOridition, pre/post test ____ _ 

Silica Gel Expanded, Y/N:, _____ _ 

Filter Condition after Test _____ _ 

Check Weight _ _ _______ _ 

Meter t.P 

Point Time Volume, ft' in. H,O 

." &\',10 q?,). ,(:.;:;V 't ...., !>,L> 'i 

'2. OCj/S :J (!).~, ~ 

I oqz<> 2, \.9.% ~ 092-' )/ 51 ,'Ii 0 ! 1-. 2..0 

'"J, (J'I27 \?.,I.'Ilo 't' \) .\0'(, 

'I.- o'H 1. 3 c9, lDiI 

I o",n 'L Q:>,11 

!?tll) oq'f~ 2!J.13 ... 4,hO I ~"J--

'~ bq 11 If ~? h.o '1 '" c> , G~ 

2. oq4 '3 (O,l;J.. 

\ ,,1-" '2. Q ,.g-;, ~p DQ.,'l 2}»).08 z.. \ ~,'i5 

., 101'1 j\,<;:,,, il2- 1\-&0>1'0 

l. I OJ}, ., ( '-2...0 

) "'2A 2. l.2.0 

@'i' iO'7'( :;Sbb ~'14 \ l'O 0 

Average: 

AMBIENT TEMPERATURE: 1 ') "10 

BAROMETRIC PRESSURE-: ~ri2-tj-;!-'';--6---:;e,,-------

ASSUMED MOISTURE: ']0/0 

PITOT TUBE COEFF, C'-p"-- : '---7'0;,·"1"1,---------

PROBE ID NO MATERIAL:jID~_<o_8=--- "~T~Q~ _____ _ 

PROBE LENGTH: <0" NOZZLEIDNO M~A~T=E~R~IA~L-: V~(~~:----------

NOZZLE DIAMETER:,_ ..:./V-=-;-: /,r-;'I-:-_______ _ 

FILTER NO/TYPE: Iv' I ,,< 

PRE-TEST LEAK RA~T"'c-::-'-: ":-z.a;+-.-'--'1?S--;"---;; C"'F;-;M-;:;@:-:e",---:i-:-n.'7H7'9-.-

POST-TEST LEAK RATE: : CFM@ in. Hg. 

PITOT LEAK CHECK· PRE: V POST: 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN -;;-A-;;-A--

SAMPLER ~M 

SAMPLEC~U~S~T~O~D~IA;-;N~A~A-,-----

t.H Stack Probe Filter Imp. Out 

in. H,O Temp, <IF Temp, ' F Temp, ' F Temp, ' F 

\~qO '\."\.o (VIA tVA b'2...b 

,Wi 

,q'O 

'1.:'l D 

I.q~ "'llb'6 ';'\2.."1 

"'10'01 " , 31 

"l'N \ 

1,'10 -. 'O~ \ '-3. <;; 

"7 "81 \ 

-,"1 "-' I 

'"'1">0 

1. 95' ,"10 ,:$''1 . '') 

,'1i 

'1'i2-

1'1-:t.-

ll/ 

\l VImp. # Contents Post-Test - Pre-Test ~ Difference 

(y),<J 1+2-'"" H1. i bio,5; 

' I 611/. (., --------- ffi l. 

.3 ,11 -I .57 C;. '7 571. 0 -----

~I j L 23'2S-'1d-.l. " ____ _ 

L .. .... -< ~Z,~"~ - / -0 C 

Total: ____ ___ ______ _ 

Meter Temp, ' F Vacuum 0 , P. static 

In Out in. Hg. % in. H,O 

10.b 12."> 5. 0 r~ <;; -t-"L.I 

1.8 . 7 "1~ . 2.- . .() 

3 " ·5 77·7 ~o 

, 

13>'12 '6'1.-/ "'.6 

I! ..... e/ 

Comments: ____________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page _1_ of _\ _ 

DS834049 

Master Document StoragelFormsl Datasheetsl Field Q;l!asheets 

" 
Oellafl. ""0.-,._""-

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: i>--<-""~ LOCATION: .. ' ~",.(..l 

DATE: 13 

RUN NO: -:l - -~ 

OPERATOR: METERBOX:~N~O~:~~~P p,~,------------

METER L1H@: I .. b '\ 

METER Yd: --="','-,,·;,.;-;1""1..------ -

STACK AREA, FT': ''f3 .. \ '1 

TRAVERSE POINT~S;-, 7M;,:IN/=p:::0It.-N-;:;T;-: -$7<71-, "' 2..-

L1H= -& X LIP: /' / 

Probe Condition, pre/post test.:-vr-__ v __ __ Silica Gel Expanded, Y/N:.--;-N"'TIr' ____ _ 

Filter Condition after Test: ' ~ I I I 

Check Weight· .. ___ _ .£0/ _____ _ 

. - --

Meter LIP 

Point Time Volume, ft3 in. H2O 

'-'J \\05 'O~q, ,qzu 14> 0."13 

2- 11 11> ? I ."Lo 

I I It:, >, 1,..2.0 

c;- P j; 1120 ((')\ \.. l 1:>, 1\ tolD 

"1> \iLL 'K XL l\;<) l'iEi I0~ 

"- 1/ 7-'1 '" b·1O 

, It ,,'- ~ \ ,\ 0 

t: O II 7;>7 1S1;Sn I· 1 ,&0 

." ((47... 'S '1'l '">57 Ii ~ lR? 

z. \\ 4 7 I, 0.&.5" 

I i IS 2- -z.. CJ . v i ') 

c,vv U>7 QbS::7 5'"2.. I 'LiD 5 

~ \"l.." .) _0.0>-7rz.. l'f'" !J. lo_'t) 

Z 1'7. ':> 7 h (1). 1')... 

/ tV' .z.. b··lH 

If" ..? 1'2-11 '111 ·33'f I C). 'W 

Average: 

AMBIENT TEMPERATURE: '-1'> 0 

BAROMETRIC PRESSURE-: - ,;)., . -::'1:-, 7&""1-------------

ASSUMED MOISTURE: ., ,/" PITOT TUBE COEFF, C'-p-: -';~:-' "'.---=D:---;q::-;Cj;:---------

PROBE 10 NO/MATERIAL:;-,o"-,,,,,x.c-s,,,f,,,,o,-_' __________ __ 

PROBE LENGTH::-:-==:O'8?-:-' __ ,--______________ _ 

NOZZLE 10 NOI MATERIAL: !Vb 

NOZZLE DIAMETER _,-I\ r(fIA- ,-,--________________ _ 

FI L TER NOITYPE ::;7-;~M"'(7'?::--:::7=;-;-;;:--T?---C:--;-;C-­ PRE .. TEST LEAK RATE:: .(o,o05 CFM@ lS in. Hg. 

POST .. TEST LEAK RATE:: 6) co<; CFM@ I ~ in. Hg. 

PITOT LEAK CHECK .. PRE: ..-- POST:'----

CHAIN OF CUSTODY: SAMPLE CUSTODIAN....:..AA""-__ __ 

SAMPLER .)1" SAMPLEC U~S~T~0~D7IA~N~:-~------

L1H Stack Probe Filter Imp. Out 

in. H2O Temp, OF Temp, OF Temp, OF Temp, OF 

2.A "1 '1 , !.rI. tv(,,\- 0<1' 

7QCC; .. ~:l"-

l'l'6 

'l'i'1 

2. .. \ 5 "1 '1 1...> 'S1I .. ., 

"l '1 (p 1 

t o, 1 ' 19 '-

2 .( , 9 ~G .. o 

-

Imp. # Contents Post-Test - Pre-Test = Difference 

t?I.).· I+;;'£ I\, 8Bz. «.::..b-'-~I1 .::...:=- ~ __ _ 

.:<. " W'I.Lj £J;id. -

3.... fi'1~ .. t/ If?' ? '1.f7 ~ 

'I !J(y "1& 0, c; 1."/1 

1-,'/.,../. fI.. \' ALx.- ...- I 00 

Total: _____ _______ _ 

-

Meter Temp, OF Vacuum O2 P. static 1 

In Out in. HQ. % in. H2O 

oro ?Jo .·1 )';"--0 (,I . , n .. .. ( 

- r 

1 

J? ~ J?oS' ~ .. C> 

8 "):..> '11-r 5 .. 0 

_f. q '-\ ~,-:E ~ 

"l"N 

'H ~ 

L·o ?1i sl.o 50,'· 3D .. ) <;,..". 

"\ ~ 

, q 

4~ 

Comments: ____________________________________________________________________________________________________________________ __ 

Date of last revision 1/2512013 Page -l- of __ ~ __ 

DS834049 

Master Document StoragelFormslDatasheetslFieid Datasheets 
Del/a~ ,,;.---

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT AMBIENT TEMPERATURE: / .L" Imp. # Content : LL: ~,..-« 

LOCATION: S,? .. .L., d ;;I... 

DATE: 1-31- J3 

RUN NO: -? ~J{ -III!!:.. -]6 fBAROMETRIC PRESSURE·-. i-'<"·l.j.,;.,-c.c..,.---rS-------

ASSUMED MOISTURE: "'\' 

PITOT TUBE COEFF, C-p-: -'::o';"''''\.~· ""-""-- - - - - --

)J r\:>U " ~t J':....:!.....:,Ic ____ _ 

PROBE ID NOIMATERI(\L:_"' ,--O_u,..,15",, · "''>''''1'''0'--____ _ _ PROBE LENGTH: ., OPERATOR: Go? METERBOX N=0'-:~qn7P~0~~-------- _____ t9·1 __ " NOZZ EIDNO M'~A~T=E=R~IA~L-:-~~~~)~-------/ 

NOZZLE DIAMETER: _____ -L:~'Ar----r"---

FILTER NOITYPE: 

PRE. TEST LEAK R""A"'T""E"': "': (.. T.=, /l?=,,-cC;;;F=-;M-;c@~---;,L,i'-n-;. H-;-g-.-

POST·TEST LEAK RATE: : -- CFM@ in. Hg. 

PITOT LEAK CHECK· PRE: v POST: 

CHAIN OF CUSTODY: SAMPL STODIAN -At-- SAM~ R 5 ,~PL 

METER bH@: I.~ '\~. METER Yd: 0 31 j: STACK AREA, FT': 1'\ .>"1 

TRAVERSE POINTS, MINIPOINT: .!{ 111.-

H= ~Xb : ' 

Probe Condition, prelpost test: _ _ __ _ 

Silica Gel Expanded, YIN: _____ _ 

Filter Condition after Test: _ ____ _ 

:USTODIAN """. 

/ 

3 

'1 

• .-1It +- .5')« . i 

':n~ 1Is.~ 

L ',,-v "- (Z,-,>-< 

--

_ ft~C 

Meter bP bH StacV Probe Filter Imp. Out Meier Temp, OF Vacuum 0 2 P. static I 

Point Time Volume, tt3 in. H20 in. H20 TelJlp,°F Temp. OF Temp, OF Temp, OF In Out in. Hg. % in. H20 

'" l '-\ 11 '19'\· o-?l S I,p 0.'; () I.e, ~ Y '" A '" r f'. '1. '1 '?'~';). 1 ':> 'a l·~·o; .... . I .'L., 1'-1 .:C"-. ? 1,2. tl ~ n·/.v 

I 1'-\:>...' J. \.:>D / l"l,) 

",iJCI I'D'1 :;..::>,:)2:)j I r"o / 1'1') 

, ~\,,' '?,o.c:·":.::0 l'f" 0 ; 1 S / 1 'S ,'1).. "I'" '1 "I. 1'-\ <:, .. 2. i '-\ 'to '; is! .'i)<Y 1, :l.. 

I \ '-\'t< i. o/f'i '1 '1,P 

e "D \ '-\ ':>D (l{ 5. 'iDl.? I /' I '1." 1 i '-f 

." Itl)7 .~ I;:4!!O "t- !J.~Cj \ .'2 1 2 ;.;;vr-~ '1'1 '" ';)- '~ 

1. / 3 O:,~ '1) 

I / L C.,S 1 I 

(el"l> / I 0 ·1'-' 1"12-

'; / 1 'ti.J ,) .1";0 ,'4 0 

'J.. ? 0, ") 0 1'1' I 

I / 11. C1 .q '\ 7 '1' "2-

f/-toJ {> / .i G.'l5' 

L /' f-

~~: ~ I 

+: " Comments: )V;1,t- V is! \ OJ:.... c:A " 

Date of last revision 1/25/2013 Page __ 1 __ of __ 1 __ DS834049 

Master Document StoragelFormslDatasheetslField Datasheets 
AMMONIA ELECTRODE CALIBRATION CURVE 

Mmple Koom 

NH3 concentration log NH, concentration Electrode potential Temperature Temperature 

(~g NH,I ml as N) (mV) (C) (C) 

1 0.000 89.4 21 21 

5 0.699 53.4 21 21 

20 1.301 18.6 21 21 

100 2.000 -21.7 21 21 

Ammonia Electrode Cal ibration Curve y = -55.7371x + 90.6621 

2/05/2013 R' = 0.9992 

100.0 

.. 

" 

iii 

'" 

0.. 

$ 

g 

S-

~ 

" 

" " 

0 

~ 

0 

~ 

-20.8 

40

60.0 

20

80

0

.

.

.

.

0 

0 

0 

0 ~ 

00 0.500 1.

~ 000 1.500 ~OO 

-40.0 

logarithm of the concentration of ammonia (~g NH, 1 ml as N) 

slope 

y-intercept 

Concentration 

~g NH,I ml as N) 

1 

5 

20 

100 

Calculation: 

-55.7371 

90.6621 

Value LR line 

1.0535 

4.6616 

19.6288 

103.7362 

Regression Line: P=M'log(~g of NH,I ml as N)+B 

Difference 

0.0535 

-0.3384 

-0.3712 

3.7362 

Measured Concentration of Ammonia (C) in ~g 1 ml NH, as N: C=10IP-BVM 

where P = electrode potential, M= slope (must be -57±3) and B= intercept 

% Difference 

5.3522 

-6.7684 

-1 .8562 

3.7362 

All standards were prepared in 0.04N H2S04 and allowed to equilibrate to room temperature. 

2. 00 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS CALCULATION 

ClienV Location: 

Sample Location: 

District Method: 

Sample Date: 

Analysis Date: 

Analyst's Initials: 

Calibration Curve: 

R' 

Sample 

GEMMA 

Sentinel Unit 2 75% 

SCAQMD 207.1 

211 /2013 

215/2013 

RF 

y= -55.7371 x+ 90.6621 

0.9992 

p Cone. 

mV 119 NH3/ml as N 

Notes: 

Measured Concentration of Ammonia (C) in "'9 NH3 ! ml as N 

C=10(p-a)lM 

P = electrode potential (mV), M=slope and B=intercept 

Average Measured Ammonia Concentration (Cavg) = (C1 + C2)/2 

where C1 , C2 results from duplicate analyses ("'9 NH3Jml as N) 

Cav9 ("9 NH,/ml as NH3) = Cav9 (" 9 NH31 ml as N)' 17.03/14.01 

).19 NH3 J sample = Cavg (119 NH3/ml as NHJ) * TV 

Used 100 ml of samples and standards with 2 ml lSA and constant stirring rale. 

Solution turned blue and remained blue with ISA. 

C avg as N 

Maximum samples (including blanks) between 28 ug/ml check standard is 5 samples and a spike 

analyzed in duplicate. 

C avg as 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS QUALITY CONTROL 

ClienU Location: 

Sample Location: 

District Method: 

Sample Date: 

Analysis Date: 

Analyst's Initials: 

Sample 

28 ug NH3 1 ml as N 

repeat 28 ug NH3/ml as N 

1-NH375% 

repeat 1- NH3 75% 

2-NH3 75% 

repeat 2- NH3 75% 

spike 2-NH3 75% 

repeat spike 

Reagent Blank 

repeat ReaQent Blank 

Field Blank 

repeat Field Blank 

DI H20 Blank 

Repeat DI H20 Blank 

28 NH3/ml as N 

repeat 28 ug NH3/ml as N 

Notes: 

GEMMA 

Sentinel Unit 2 75% 

SCAQMD 207.1 

2/1/2013 

2/5/2013 

RF 

% recovery 

NA 

NA 

NA 

98.83 

NA 

NA 

NA 

NA 

spike: 100 ml sample + 2 ml (1000 f!g NH3 1 ml as N) 

Matrix Spike Percent Recovery (%R) 

%R = (C spike*0.1 04 - Csample*0.1 02)/2 *100 

Cspike = average result of matrix spike (f!g NH,I ml as N) 

RPD 

% 

-0.83 

-1 .24 

-3.72 

0.00 

1.65 

-2.07 

2.07 

0.00 

RPA 

% 

0.008 

NA 

NA 

NA 

NA 

NA 

NA 

0.007 

Relative Percent Difference (RPD) = (C1-C2)1 Cavg *100 (must be 5% or less) 

Relative Percent Accuracy (RPA) (must be 10% or less) 

RPA = (Cavg-theoretical value of standard)1 theoretical value of standard * 100 
N<Qt..ooIiIy

8ella~ . __ "'" 

AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS 

Project #: District Method: SCAQMD 207.1 Sample Date: 2./ ( /13 

Client/Location: G £ M fl'11t Calibration Date: 2lfll3 Analysis Date: zL5/ 13 

Sample Location: .s:u,L"~t.{ U 2.. Calibration Curve: IP-~. 7J,IK-,196.U 21 Analyst's Initials: R l' 

Test #'s: 7~ % R': 0 . 991'2... I 

Sample Electrode TV Cone. Cavg g NH31 Commentsl Temp/pH 

Potential (ml) ~g NH3- (fig NH3 sample 

(mV) N Iml - N I ml) 

Standard Check: Percent Recovery: 

28 ~g NH,tml 

/0 . / 27.'OH 

Repeat 28 9, 'j 2 f.//f 2 f.. 6 c> 'Z-

/-!J!/, - 15! '(,.] J. flo 

~t llVt/,-is/. 7t.o Vcs J.f33 /.f.2/ /b 27. 4( iJ/! L. 1.. T'" 2. / ~ 

2- }/1I;- 7S! 7LI·3 /. '7(,(., 

0 Pe./Je d 2. -JIll, . 15. '/. 71. (I S l>o 2. _O'(() 2 -60.3 /2. 111 .'1 pI! < 2. j-= 2/c. 

< 1» 1/, 2.;./1/,-:75'1 /?C> 21>·1 7-0 

ReMt;i 5;/1<~ {t ·O 20>.'11 0 LI!>·tj1o Du. ut/ 7<f% 

Re:.~i R!Ov\K /SI,o I 

().CJt3 

Rd~a c RI& /S/·'I ". o~ I O·Ob20 

F/~{c1 P. fw.K 11 5.'( O·.3M' A/I 50)vllD>1,S 

P,<.,.u.:t FA /1/{,9 tJ.3C7- 6· 3(3C. Leded c.t 

(jl 1./, 6 n./"", f 135.' 6 ./5(, Z l 0 c. 

Re../le.d fJ/IILo 8,11< /3('. ( ()./S3 ()./sW 

1.. K- Aill, (b.O ~·C/Ol. 

R.2 /'€~ I:. 2 P J/ /I, /tJ·O 2. f. Ot> L 2 g.O()'l. 

Notes: Total volume of samples and standards used: 100 ml 

Volume of pH adjusting ISA used in ml: 2 ml 

Absorbing solution: 0. 1 N H2S04 

Calculations: Conc. ~g NH3 - N I ml) = 10 (P·8)IM 

P = electrode potential, B = y-intercept and M = slope 

Cavg = average result of duplicate analyses (~g NH3 - N I ml) = (C1 +C2)/2 

~g NH31 sample = Cavg* 17. 031 14.01 * TV 

mg I sample = g Isample .,. 1000 

ppm NH3 = mg NH,tsample x 1Nmstd x 1/454000 x SV/1 7 x 10· 

De/tat:.. 

--

Date of last revision 12/5/2 008 

D8834059 

Master Document StoragelFormslDatasheetslLab Forms 
AMMONIA TEST RESULTS SUMMARY 

CPV 

60 60 

1/30/20 13 1/3012013 

SCAQMD 207.1 SCAQMD 207.1 

9-P&M 9·P&M 

0.992 0.992 

143.14 143.14 

60 60 

12:17 15:05 

49.350 47.820 

75.9 67.5 

1.80 2.00 

118.4 116.0 

12.98 12.97 

2.49 2.25 

103 103 

47.521 46.802 

0.104 0.103 

339,745 344,040 

Pressure (lbf/ft2) 211S.224 2116.224 

Molecular Weight NH3 (tbllb-mole) 17 17 

Specific Molar Volume (ft3/1b-mole) 379.50 379.50 

Mass Conversion (fb/ug) 2.20E·09 2.20E·09 

02 Correction Factor (%) 15 15 

Mass NH3 (ug/sample) 1801 .55 2082.66 

Mass NH3 (mg) 1.802 2.083 

NH3(lb) 3.97E-OS 4.59E·06 

NH3 EQUATIONS: 

ppm NH3 = (mass NH3* Gas Const'" Ref Temp ... 10S )/(Sample vol. ... Press' MW) 

ppm NH3 @02correction= ppm'" (20.9-02 Corr)/(20.9-%02) 

12.98 

2.37 

2.0 

i , 
""ClooItf De//a __ ~ 

CLIENT: C,eM M A 

LOCATION: YWTC/JAk (},;f zDATE: 113 D li 3 

RUN NO! .s ;[ S"It~ .. - N\t3-\OO-\ 

OPERATOR: ~.,) "'-

METER BOX NO:_S::..l..":...; p."",;.c-__ _ 

METER &H@:.....-c'",," *3-=l\--, '\~ ____ _ METER Yd: 0 5.L. 

STACK AREA, FT..,: !..:l( ",.,J'i~~~_~ 

TRAVERSE POINTS, MIN/POINT: 'l""' A /1'--

&H= 1. 0 X &p' /' 

Probe Condition, pre/post test--"Cf.{'-'::'/ __ 

Silica Gel Expended, YIN: ",7 

Filter Condition after Test---'''''~Pr '----- Check Weight __ ......e:./ ___ __ _ 

Meter &P 

Point Time Volume, ft3 in. H,O 

~ 

3 I\b'[ U~:r.,8:;o '1'" \,'J., 

l \1 or. 3 i-<'-.> 

I \ 1 01\ 1. t~ 

eN" I \ I l<o I '+4%,b'l0 I \. ::'> 

'" , ilZh 4 '{t,b )"0 't~ ilL '60 

2- tV>, 1 5 00,\ 

I tl '!><i ~ 1"3 .:"~ ll'-* I 14t.6,~0D I \ ,z. -"> \ \ 1..\ , Q-( .. I! .S'11 4 N /) ."10 

;; 1 \ c::tJ 1, 0 . 1';5 

I \ l ., S '2.. /),"15 

",,"11> \ 7..0D "\1Jv 10' I In " \'L01.. '-\ l~1bc) ~u.) n"1)" 

7 \201 " o ,..J'-\ 

I \;!.\;... < 01.1'> 

i J..q "\,'65', 'lbu \ \. \ 

Average: 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET 

AMBIENT TEMPERATURE: ,20 

BAROMETRIC PRESSURE-: Z:;-;~;=,3';;;O=--------

ASSUMED MOISTURE: q '~ 

PITOT TUBE COEFF, Cp: IV I ~ 0 Lj<j 

PROBE ID NO/MATERIAL:---.::o'-'O,;..:...!L..;'L'--S"-( !..I D _ ____ _ 

PROBE LENGTH: b NOZZLEIDNO/M~A~T~ER~I~AL:-N~/ C--------

NOZZLE DIAMETER:_ -","'tI"'A-" -'-_______ _ 

FILTER NOITYPE: & ( Pc 

PRE-TEST LEAK RA==T==E'- : -: ">Z+-o"' • .::>o ---=,.-=C"'FM"'@-=-'I-..S- ---cin-.7H,-g-. 

POST-TEST LEAK RATE: : 4.vlz(CFM@ ,." in. Hg. 

PITOT LEAK CHECK - PRE: v- POST:--

CHAIN OF CUSTODY: SAMPLE CUSTODIAN ....... 

SAMPLER ;;5 

SAMPLE CUSTODIAN ~ 

&H Stack Probe Filter Imp. Out 

in. H,O Temp, OF Temp, OF Tem . OF Temp. OF 

~ Ii A 'T tv f\ 

vt 1 l '> "I ,) 

"t"t"'i 'f 1,'< 

Tl~ 

. 7'7 ~ b1. <a 

'2J.-

,1)... 

1 I") 

,1'0 ton 

1'10 

110 

1'1 [ " 

1 [oL " '5" 1 

1,1 ',d.. 

"").... / \ ' " 

I 

Imp. # Contents Post-Test - Pre-Test = Difference 

~ IN\~z.~ rh,! b613"--__ 

J... D.I fl\\ • .5Z:\ G:wlj.u l..(,3, 2 __ _ 

~ I\J.-"\ t-(q 03 ~rfl ;:\-'--__ 

'"t ';)0 111{.iJ; 9?:o.j __ 

\)1:- ~o hN<3 (2-~ _ \=.u 

Total: ____________ _ 

Meter Temp, OF Vacuum 0, Pstatic 

In Out in. HQ. % in. H,O 

13,) ,\-" .·6 

M ., <D-o 

I 

177.') 11-J 5--0 

'19 1.3 ""D 

,5 .,:>- 1>-/ . 

\ 

Comments: ·J'e..l o ct.~ ST A'r>-, e:p \\05' 

Date of last revision 11/13/08 

OS834048 

Master Document StoragelFormslDatasheetslField Oatasheets 
, 

Della/),. 

.. o..w,.-. ... ..-.. 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: t0c ~ '" .y 

LOCATION: 5", h,'d~ ( :t-., 

DATE: 1-10' 13 

RUN NO: .3. W -Nlh- I"'<D<~ OPERATOR: 6.3 METERBOX7N~0~:~q~P ~~-----------

METER 6H@: \- 0~q METER Yd: - -;,fJI;-• .z'l,;,c,

C:L------ -

STACK AREA, FT': Ic·n . \ 'f 

TRAVERSE POINTS, MIN/POINT: iiI i:l. 

H= ~X6 : /' / 

Probe Condition, preipost test: v . Silica Gel Expanded, Y/N:."L/ -:t.J76;-____ __ Filter Condition after Test: 7 iJ1!I 

Check Weight: _ _ _ -"v ___ ___ _ 

Meter 6P 

Point Time Volume, ft' ,in, H2O 

S , ,3 \I 'l%~M 't"" " olG 

'L l'3 ' l,> I:) ~ ,':'1,0 

I iJ "-I >- <!l, Y\ 

IZ{\)O L j'2.Le 'h'-<, '-( ~'> II \ • 30 

16' '7 r5'!:>i »t"q, 't", <;' 1'-1 ~,'10 

Z. 133(0 "> 10,'02. 

I L '041 'l. I) 0 D ::~ 51!.{{; I Q) .< ~Ij 

") 1,,\'-'6 <)U ,liJ .. /), 'l! ,"" t \'-\ ')'> .; Q,O 

I 1"1 :''b ~ \''L 

€">D I" 't,,) r; 'z,2,",O \ \' <;-

? I \ '7u 521. ,'ilt? L\ \,\. 

1. 1 ' ,~ ? \ .. So 

\/' I \ ~ 'I. "I ' \0 

E:' "Ill> \ ~ 1>"- 2'q., "Ion I Vi 

Average: ..... . , -. Comments: .It 13~~ -~~ :mDate of last revision 1/25/2013 

, 

-'" AMBIENT TEMPERATURE: ,.> BAROMETRIC PRESSURE: - "",~"","", , '6"'''''=''-------------- ASSUMED MOISTURE: -'L---

PITOT TUBE COEFF, C'-'-p-: - o;:;,,,c,.r.--------- PROBE ID NOiMATERIAL:--'.>I-='-"'-______________ _ 

PROBE LENGTH: ~ \ NOZZLEIDNO/M~ E~R~IA --~N;-A---------------

NOZZLE DIAMETER:· ________ "_"n' "'/.\io------------ FILTER NOfTYPE: - :J Ilf 

PRE-TEST LEAK RATE: : La,,,,,,> CFM@ I <C: in, Hg, 

POST-TEST LEAK RATE: : <.$,;;0:) CFM@ { ~ in, Hg, 

PITOT LEAK CHECK - PRE: v- POST: ......... 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN "-4 

SAMPLER ~ 

SAMPLE CUSTODIAN h:±. 

6H Stack Probe Filter Imp, Out 

in, H2O Temp, OF Temp, OF Temp, OF Temp, OF 

;;. - () ,I,') ("ill,: N ,n '-1\ 

'1 l'-f 

"1 1::> 

,7,-". ~J.. ,j) '11~ H.v 11~< 

"1 lip 

1" Pi 

1'1'> / '-\9 

-1'1('" 

7"~ 

Ill: 

" '-\,\. 

." "1 't 

'1'bD 

79,(\ 

I-- , 

Imp, # Contents Post-Test - Pre-Test = Difference 

tP·);.;lhj • ..., J>n ,\ ~f'i:!e 

J.. ~ (;bS f tlvl{.v 

3 .N1.t' ..5"10, 1 6 711 

vi .jL~ 9 J F,'1 .tcc'll. 

L I' M.. £. .. &,;.. -/roO 

Total: ____ _________ __ 

Meter Temp, OF Vacuum 0 2 p, static 

In Out in, Hg, % in, H2O 

to'i \.6'1 S'-D I'",,/<. ~:<., \ 

" 

"""I. G., ::;'0 

Co 'L '-''3 .>;; y') 

1 

C;,(; "'~ " ' J 

Page __ of __ 

DS834049 

Master Document Storagel Formsl Datasheetsl Field Datasheets 
... 

Della~ _...., ... ,-

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: !Y '-/'Y'~ LOCATION: 3:i "f,'-<--Y{ t:{,;v ~ t % 

DATE: ;).-1 ~ ;3 

RUN NO: ~- ;;)./6 - Ai I",PiS'· I 

OPERATOR: .55' METERBOX~N~O~:L-5~~~~ ------------

METER 6H@:----'I>--=-'6liJll:I~L:__:c:::_:_-- METERYd: c· 11l--

STACK AREA, FT': 

TRAVERSE POI NT~S:-, :eM "'I N"'/"'P"'O"' I N"'T""': --:-,,"'4'--- H= X6P: / 

Probe Condition, pre/post test: / 

Silica Gel Expanded, Y/N:* 

Filter Condition after Test: 

Check Weight: . 

Meter 6P 

Pqij1t Time Volume, ft3 in. H2O 

'7\' IO"l9') q, 'n-, '{"It 

Average: 

AMBIENT TEMPERATURE: r,,2:: BAROMETRIC PRESSURE-: ----,L~1:"Wib-----

ASSUMED MOISTURE: 

PITOT TUBE COEFF, C'-p-: --- , ,;--, -r} --- ----

PROBE ID NO/MATERIAL: ___ ---t,L-______ _ 

PROBE LENGTH: 7 

NOZZLE ID NO/ MATERIAL: i A 

NOZZLE DIAMETER:. _____ -'--_____ _ _ __ 

FILTER NOfTYPE: 

PRE-TEST LEAK R;:-A:-OT"'E""':-: <;--". Oi>----;r".C~F=:M--:-@~---;---::S~-i:---c , H--:-g-,-

POST-TEST LEAK RATE: : CFM@ in,l{q, 

PITOT LEAK CHECK - PRE: f'-I (,(\- POST: llJ f\' 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN-,--,-__ 

SAMPLER ~> 

SAMPLE CUSTODIAN 

6H Stack Probe Filter Imp. Out 

in. H2O Temp, OF Temp, OF Temp, OF Temp, OF 

I } 

[ ./V' 

y' VI J 

V ¥ iI "'---

\ ~ 1'11. IV 

_'\6\ r' ~ / 

-- -- .. -

Imp. # Contents Post-Test - Pre-Test = Difference 

_1 ~-I": I/-->-j., 4' ~ Yi1-Z 

"-- , , 1 1;-9 

3 ,,,", -!- f;,GI.3 

i ~ (i" 2~7 g 

L....~ '~ jzl' ..... .."~ - ;c[, 

Total: _ _________ _____ _ 

Meter Temp, OF Vacuum 02 p, static 

In Out in, Hg. % in, H2O 

Commenffi: ____________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page __ of __ 

DS834049 

Master Document StoragelFormslDatasheetslField Datasheets 
AMMONIA ELECTRODE CALIBRATION CURVE 

:sample Koom 

NHJ concentration log NH3 concentration Electrode potential Temperature Temperature 

(~g NH3 1 ml as N) (mV) (C) (C) 

1 0.000 89.4 21 21 

5 0.699 53.4 21 21 

20 1.301 18.6 21 21 

100 2.000 -21 .7 21 21 

Ammonia Electrode Calibration Curve y = -55.7371x + 90.6621 

210512013 R' = 0.9992 

100.0 

" 

ES-

'" 

Q. 

n; 

2 

0 

0 

<l> 

t: 

40.0 

60.0 

20.0 

80.0 

~ .. ~ 

-- 0.0 " 

iii " 

-20.&' 00 0.500 1.000 1.500 ~oo 

-40.0 

logarithm of the concentration of ammonia (~g NH31 ml as N) 

slope 

y-intercept 

Concentration 

(~g NH31 ml as N) 

1 

5 

20 

100 

Calculation: 

-55.7371 

90.6621 

Value LR line 

1.0535 

4.6616 

19.6288 

103.7362 

Regression Line: P=M'log(~g of NH,t ml as N)+B 

Difference 

0.0535 

-0.3384 

-0.3712 

3.7362 

Measured Concentration of Ammonia (C) in ~g 1 ml NH3 as N: C=1 (P·B~M 

where P = electrode potential, M= slope (must be -57±3) and B= intercept 

% Difference 

5.3522 

-6.7684 

-1.8562 

3.7362 

All standards were prepared in 0.04N H2S04 and allowed to equilibrate to room temperature. 

2. 00 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS CALCULATION 

ClienV Location: 

Sample Location: 

District Method: 

Sample Date: 

Analysis Date: 

Analyst's Initials: 

Calibration Curve: 

R' 

Sample 

GEMMA 

Sentinel Unit 2 100% 

SCAQMD 207.1 

2/1/2013 

2/5/2013 

RF 

y= -55.7371 x+ 90.6621 

0.9992 

P Conc. 

mV ~g NH3/ml as N 

28 ug NH3 / ml as N 10.0 

repeat 28 ug NH3/ml as N 10 

1-NH3100% 59.0 

repeat 1- NH3100% 59.4 

2~NH3 100% 60.8 

repeat 2- NH3 100% 60.9 

spike 2-NH3 100% 15.1 

repeat spike 15.1 

Reagent Blank 151.0 

re~eat Reaqent Blank 151.4 

Field Blank 115.4 

repeat Field Blank 11 4.9 

DI H20 Blank 135.6 

Repeat DI H20 Blank 136.1 

28 NH3/ml as N 10.3 

repeat 28 ug NH3Iml as N 10.2 

Notes: 

Measured Concentration of Ammonia (C) in ).19 NH3! ml as N 

C= 1 O(P-S)IM 

P = electrode potential (mV), M=slope and B=intercept 

28.002 

28.002 

3.699 

3.638 

3.434 

3.420 

22.682 

22.682 

0.083 

0.081 

0.360 

0.367 

0.156 

0. 153 

27.657 

27.772 

Average Measured Ammonia Concentration (Cavg) = (C1 + C2)/2 

where C1, C2 results from duplicate analyses ().lg NH3/ml as N) 

Cavg (~g NH,Iml as NH3) = Cavg (~g NH31 ml as N)· 17.03/14.01 

).lg NH31 sample = Cavg (I-'g NHiml as NH3) * TV 

Used 100 ml of samples and standards with 2 mllSA and constant stirring rate. 

Solution turned blue and remained blue with ISA. 

CavgasN 

28.002 

3.668 

3.427 

22.682 

0.0820 

0.3636 

0.1546 

27.714 

Maximum samples (including blanks) between 28 ug/ml check standard is 5 samples and a spike 

analyzed in duplicate . 

TV C avg as NH3 ).19 NH31 

(ml) sample 

NA 34.038 NA 

404 4.459 1801 .548 

500 4.165 2082.655 

NA 27.572 NA 

NA 0.100 NA 

350 0.442 NA 

NA 0.188 NA 

NA 33.688 NA 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS QUALITY CONTROL 

ClienV Location: 

Sample Location: 

District Method: 

Sample Date: 

Analysis Date: 

Analyst's Initials: 

Sample 

28 ug NH31 ml as N 

repeat 28 ug NH3/ml as N 

1-NH3100% 

repeat 1- NH3 100% 

2-NH3 100% 

repeat 2- NH3 100% 

spike 2-NH3 100% 

repeat spike 

Reagent Blank 

repeat ReaQent Blank 

Field Blank 

repeat Field Blank 

01 H20 Blank 

Repeat 01 H20 Blank 

28 NH3/ml as N 

repeat 28 ug NH3/ml as N 

Notes: 

GEMMA 

Sentinel Unit 2 100% 

SCAQMD 207.1 

2/1/2013 

2/5/2013 

RF 

% recovery 

NA 

NA 

NA 

100.47 

NA 

NA 

NA 

NA 

spike: 100 ml sample + 2 ml (1000 ~g NH31 ml as N) 

Matrix Spike Percent Recovery (%R) 

%R = (C spike'0.104 - Csample'O. 1 02)/2 '100 

Cspike = average result of matrix spike (~g NH,I ml as N) 

RPD 

% 

0.00 

1.65 

0.41 

0.00 

1.65 

-2.07 

2.07 

-0.41 

RPA 

% 

0.007 

NA 

NA 

NA 

NA 

NA 

NA 

-1.020 

Relative Percent Difference (RPD) = (C1-C2)1 Cavg '100 (must be 5% or less) 

Relative Percent Accuracy (RPA) (must be 10% or less) 

RPA = (Cavg-theoretical value of standard)1 theoretical value of standard' 100 
AMMONIA BY ION SELECTIVE ELECTRODE ANALYSIS 

Project #: District Method: SCAQMD 207.1 Sample Date: 21 1/13 

Client/Location' G £ M fI"!;4 Calibration Date' 2/5113 Analysis Date: 7.15113 

Sample Location . .s..nt"~<.1 u Z. Calibration Curve: I/.:.-SS. 73,1 K-,I<j6.U 21 Analyst's Initials: R"-

Test#'s:_-<-J",o-=o:....%'-!p",-__ R2: O. 7912... 

I 

Sample Electrode TV Cone. Cavg fI9 NH31 Commentsl Temp/pH 

Potential (ml) fIg NH3- {fI9 NH3 sample 

(mV) N/ml - N 1 mil 

Standard Check: Percent Recovery: 

28 ~g NH,iml 

/6·0 U.6C>2.. 

Repeat 28 /{),C; Zf.oo2.. ~ f.(jo2, 

/-/JI/~ -Ivc>~~ S"(·O 3 .(.."}'1 

~t I·NtI, -I(>O/r- 5'1. (I L/o", 3 .f..~f- 3 ·CoU· /,fc>I.S Ill/'/' 2.. T.:: '2I>CC 

2 - IV 11,-locI. W·F ? ·1 jJ.f 

Re./Je d 2· J/ fI, -I oc!!, &0·9 SOD 3. «( 20 3 .1{2.1 2i!>f2 . C, ,>I/.c: 2 T=.2I"cC"l". 2.JlI/, -Ioo/. 15./ ntn 

Re Aet;{ 5P,'WL / .$./ ZZ·Cf2. 2,2 .(;f2.. D. UL/ /60% 

Re:..~i R/r;..r.K I S/.O 6.of? 

, 

R (..-j~G C R. IS /S/,4 t).o~1 D. 6 ~'2.0 

Ft'elci n.ic.v.. K I{S. L( 0,3(..0 IAII SolvilDrlS 

l<<./lR&t Ff.? /11.[. " 0 , 3(,1 (')·3f,3? LedecJ c..t 

iJl /../, is f?1v.-. t /'3,5. (, 6./5(, 2. I 0 

C 

Re.;'Je.d IJII/L o.6/ J< !?I.-, ( 0./&1 f). WIt 

2. of Nil ... /b.3 2 ':J. t.S'lR.fl.;.€4/; 2N/J./, 1°.1. 27. Ttl. 2t-. T I I.f 

Notes: Total volume of samples and standards used: 100 ml 

Volume of pH adjusting ISA used in ml: 2 ml 

Absorbing solution: 0.1 N H2S04 

Calculations: Conc. (fIg NH3 - N 1 ml) = 10 (P,SlIM 

P = electrode potential. B = y-intercept and M = slope 

Cavg = average result of duplicate analyses (fIg NH3 - N 1 mil = {C1+C2)/2 

fIg NH31 sample = Cavg* 17.03/14.01 * TV 

mg 1 sample = fIg Isample ... 1000 

ppm NH3 = mg NH"Isample x 1Nmstd x 1/454000 x SV/17 x 106 

De/tab. "'_ ......... ,-

Date of last revision 12/5/2008 

D8834059 

Master Document StoragelFormslDatasheetslLab Forms 
Appendix C.4 SOx by SCAQMD Method 307.91 

R0410673 C-8 .. De/ta _ ....... , ... -

~ 
Parameter 

SOx 

Units 

Ib/MMBtu 

Ib/MMscf 

grH2S/100se! 

Max 

Result 

0.00003 

0.034 

0.013 

Limit Rule 

0.06 40 CFR 60 

0.67 Rule 2011 

0.25 SCAQMD Permit 861.1 
Sentinel 2 Fuel Analysis and Sulfur Cales 

Sulfur 

Client 

Facility 

Unit 

Gemma 

CPV Sentinel 

2 

CPV Sentinel-2-Fuel-1 &2 

HHV 

Fuel Sulfur Content, (BTU/ft3 MW MW 

ppmv @60F) (H2S) (S02) 

Result 0.20 1014.3 34.00 64.00 

Limit 

Reference 

gr/100 scI = ppmv lue1/10·6 x MW (H2S)/SV x gr/lb x 100 

Ib/10·6 set = ppmv lue1/1 0·6 x MW (H2S)/SV x 10·6 

Ib-S02lMMBtu = ppm lue ~1 0·6 x MW (S02)/SVlHHV x 10·6 

(Specific 

Molar 

VoJume@ 

60F) 

379.5 

gr/lb 

7,000 

gr-H2S/100 

scI 

0.013 

0,25 

SCAQMD 

Permit, 

B61.1 

IbsH2S/MMsel 

0.018 

0,690 

Rule 2011 

IbS02/MMBtu 

0.00003 

0.06 

40 CFR 60 

2/1412013 

3:37 PM 
Client 

Facility 

Unit 

Load, 

MW 

101.0 

Gemma 

CPV Sentinel 

2 

Fuel Sulfur Content, 

ppm 

10.20 

Sentinel 2 Fuel Analysis and Sulfur Calcs 

SOx 

CPV Sentinel-2-Fuel-1&2 

Specific 

Molar 

Volume Stack 

(SV), Flow Rate Fuel Flow 

dscf/lb- (Qsd19), Rate, 

mol dscfm hscf/h 02 Ib/hr, S02 

379.5 362,515 8319.3 13.13 0.02806 

S02 Ib/hr = (sulfur ppmv)/1 0'6 x (MW S02)/SV x hscf/hr x 100 scf/hscf 

ppm S02 = Ib/hrx SV/MW x 1/Qsd19 x 10'6160 

Stack flow rate, fuel flow and 02 in conjuction with PM tests at 100% load condition 

ppmv@ 

ppmv 15% 02 

0.008 0.006 

S02, 

Ib/MMscfFuel 

0.034 

2/14/2013 

3:44 PM 
Client 

Facility 

Unit 

Carbons 

1 

2 

2 

3 

3 

4 

4 

4 

4 

4 

4 

4 

5 

5 

6 

Gemma 

CPV Sentinel 

2 

Compound 

Hydrogen 

Carbon Dioxide 

Carbon Monoxide 

Nitrogen 

OXVQen 

Methane 

Ethylene 

Ethane 

Propane 

Propylene 

Isobutane 

n-Butane 

1-Butene 

Isobutylene 

t-2-Butene 

c-2-Butene 

1,3-Butadiene 

Isopentane 

n-Pentane 

HexanesPlus 

Compound 

Total Reduced Sulfur 

FUEL F-FACTOR CALCULATIONS 

CPV Sentinel-2-Fuel-1&2 

1 2 Average 

detect? MOLE % detect? MOLE % detect? I MOLE % 

< 0,001 < 0,001 < 0,001 

0,538 0,555 0,547 

< 0,001 < 0,001 < 0,001 

4,778 2,475 3,627 

0,037 0,015 0,026 

89,675 91 ,836 90,756 

< 0,001 < 0,001 < 0,001 

4.360 4,481 4,421 

0,480 0,494 OA87 

< 0.001 < 0.001 < 0,001 

0.034 0,036 0,035 

0,057 0.058 0,058 

< 0.001 < 0,001 < 0,001 

< 0.001 < 0,001 < 0,001 

< 0.001 < 0.001 < 0.001 

< 0,001 < 0.001 < 0,001 

< 0.001 < 0,001 < 0,001 

0,012 0,013 0,013 

0,009 0,014 0.012 

0,020 0,022 0,021 

detect? ppm detect? ppm detect? ppm 

0,2 0,2 0,20 
FUEL F-FACTOR CALCULATIONS 

Client Gemma Unit 2 

Facility CPV Sentinel 

CPV Sentinel-2-Fuel-1&2 

SPECIES MW MOLE% MW*% HHV BTUlSCF C H 0 

CO2 44 0.547 24.05 0.07 0.00 0.17 

CO 28 0.001 0.03 3210 0.003 0.00 0.00 0.00 

N2 28 3.627 101 .59 0.00 000 000 

O2 32 0.026 0.83 0.00 0.00 0.01 

C1 16 90.756 1456.0 1012.0 91845 10.89 3.63 0.00 

C2 30 4422 132.95 1773.0 78.39 106 0.27 000 

C3 44 0488 21 .52 2524.0 12.32 0.18 0.04 000 

C4 58 0.098 5.66 32710 3.19 0.05 0.01 0.00 

Cs 72 0.024 1.73 3998.0 0.96 0.01 0.00 0.00 

Cs+ 86 0.021 1.81 4743.0 1.00 0.02 000 0.00 

Ave. / Total 100.01 1619.63 1014.30 12.20 3.95 0.00 

Weight, % 99.74 75.35 24.39 0.00 

GasMW 16.20 

Btu/set= 1014 @60F 

Btu/set= 1030 @68F 

Btu/lb.= 23,766 

Ib.lscf= 0.0427 

Fd"(60)= 8,456 (02 Based) 

Fd"(68)= 8,586 

Fc"(60)= 1,002 CO2 Based) 

Fc"(68)= 1 ,018 

Calculations: 

Fd"(68) = 1 0'6 * [3.64 * (H%) + 1.53 * (C%) + 0.14 * (N%) - 046 * (0%)]/ HHV, Btu/lb 

Fd"(60) = Fd"(68) * 520 R / 528 R 

FC"(68) = 1 0'6 * [0.321 * (C%)]/ HHV, Btu/lb 

Fc"(60) = Fc"(68) * 520 R / 528 R 

N 

000 

0.00 

1.02 

0.00 

0.00 

000 

0.00 

0.00 

0.00 

0.00 

0.00 

0.00 
Sentinel 2 Fuel Analysis and Sulfur Cales 

F-Summary 

Client 

Facility 

Unit 

Gemma 

CPV Sentinel 

2 

CPV Sentinel-2-Fuel-1&2 

Gas MW 16.20 

Btu/scf= 1,014 

Btu/scf= 1,030 

Btu/lb.= 23,766 

Ib.lscf= 0.04268 

Fd"(60)= 8,456 

Fd"(68)= 8,586 

Fc"(60)= 1,002 

Fc"(68)= 1 ,018 

2/14/2013 

3:32 PM 
Parameter Method No. Method Title 

Fixed Gases ASTM D1945/1946 Analysis of Natural Gas/Reformed Gas by Gas Chromatography 

HHV ASTM D3588 Calculating Heat Value, Compressibility Factor, and Relative Density of Gaseous Fuels 

Sulfur ASTM D5504/SCAQMD METHOD 307-91 Determination of Sulfur Compounds in Natural Gas and Gaseous Fuels by Gas 

Chromatography and ChemiluminescencelDetermination of Sulfur In A Gaseous Matrix 
Appendix C.5 ROG by Modified SCAQMD Method 25.3 

R0410673 C-g 
Client/Location Gemma CPV Sentinel 

Unit 2 

Sample Location Stack 

Test No. S-2/STK-ROG-50-1 A 

Date 2/1i2013 

Test Method Modified SCAOMD 25.3 

Sample Time (HH:MM) 1 :15 

Start Time 14:20 

Stop Time 15:35 

Stack O2 (%) 14.38 

Results 

Canister NMNEOC (ppm) 0.79 

ROG, ppm' 0.79 

ROG, ppm @15% O2 0.71 

RPD2

, % - 1) Includes bias correction of 1.086 

2) Relative percent difference less than 20% 

3) Samples were collected simultaneously as a pair 

Results at PQL level 

Reference Temp (F) 60 

Data By AA, SP, SS, JM 

S-2/STK-ROG-50-1 B Average 

2/1/2013 

Modified SCAOMD 25.3 

1 :15 

14:20 

15:35 

14.38 

0.72 

0.72 0.76 

0.65 0.68 

- 4.6% 
Client/Location Gemma CPV Sentinel 

Unit 2 

Sample Location Stack 

Test No. S-2/STK-ROG-15-1A 

Date 2/11201 3 

Test Method Modified SCAOMD 25.3 

Sample Time (HH:MM) 124 

Start Time 9:10 

Stop Time 10:34 

Stack O2 (%) 13.47 

Results 

Canister NMNEOC (ppm) 0.68 

ROG, ppm' 0.68 

ROG, ppm@15%02 0.54 

RPD2

, % - 1) Includes bias correction of 1.086 

2) Relative percent difference less than 20% 

3) Samples were collected simultaneously as a pair 

Results at PQL level 

Reference Temp (F) 60 

Data By AA, SP, SS, JM 

S-2/STK-ROG-75-1 B Average 

2/1/2013 

Modified SCAOMD 25.3 

1:24 

9:10 

10:34 

13.47 

0.70 

0.70 0.69 

0.56 0.55 

- 1.4% 
Client/Location Gemma CPV Sentinel 

Unit 2 

Sample Location Stack 

Test No. S-2/STK-ROG-100-1A 

Date 1/30/2013 

Test Method Modified SCAQMD 25.3 

Sample Time (HH:MM) 1 :09 

Start Time 11 :01 

Stop Time 1210 

Stack O2 (%) 12.98 

Results 

Canister NMNEOC (ppm) 1.01 

ROG, ppm' 101 

ROG, ppm@ 15% O2 0.75 

RPD2

, % -

1) Includes bias correction of 1.086 

2) Relative percent difference less than 20% 

3) Samples were collected simultaneously as a pair 

Run 2 at PQL level 

Reference Temp (F) 60 

Data By AA, SP, SS, JM 

S-2/STK-ROG-1 00-1 B Average 

1/30/2013 

Modified SCAQMD 25.3 

1 :09 

11 :01 

12:10 

12.98 

0.62 

0.62 0.82 

0.46 0.61 

- 23.9% 
Client/Facility: 

Unit/Location: 

SCAQMD METHOD 25.3 

EVACUATED CANISTER SAMPLING DATA 

(],,;- rq /'{ iT Date: CJ-// / 0 --~~i~~,L-~--------------

(It!, f Z. 'Sf; ,/'/ ;,4- Performed By: ___ 7.<..'"-- ) ____________ __ 

Probe Material _________ """-> _5'----_______ Probe Length __ ---"' 6=-____________ __ 

Connecting Tubing Material, __ -L:t-Ic... >A ______ Connecting Tubing Length __ ..:::lJ::......:4 ______ _ 

Barometric Pressure ____ ..:;2...::."........., ·(o=..5-".'--____ .Ambient Temperature ____ l .!..."2.::.;::..b ______ _ 

Test No. s"-;2. - s (I<. . ~G- >,' _I e S - 2 ··· s//-<; -R'ft;;:JiI- 1:5 

ViaiiD Nt\- __ AlrtCanister ID '5 5 2--- <-/5 '3 

Time Vacuum Time Vacuum Time Vacuum 

Pre-Test Leak Start (01 2,/ /r:;2- C/ 2'7 Check / ;2'0 

Pre-Test Leak Stop ; (/ j{ '2 5 I,)] V Check 'Z-:J / 

Sample Start 

Collection / 

b;,.l ;;1.1" 

" 

\~.'ZD \ Lj2-0 f 0.'0 

I 

S i --I. '3, ''I 2 S-tl l+3,'\ 2C;'-f 

I 

LlJ ISo I '20 v. ISelj 2..0\\ 

Sample Stop I~ l ')3>)" l()li 1C;35 \0 ,I Collection 

Post -Test Leak Start " I(;./u , , 

Check /6/0 1 0) /J 

Post-Test Leak Stop i6:2c.J ,/ 

/0 // 

Check /d /6;{ 0 

/ 

Line Rinse 

Volume ./ /" / ~ / 

Comments: __________________________________________________ _ 

Dellaf). 

... <>.oIdy ....... . . .......... ... 

Date of last revision 11/13/08 

DS834043 

Master Document StoragelFormslDatasheetslField Datasheets 
SCAQMD METHOD 25.3 

EVACUATED CANISTER SAMPLING DATA 

ClientlFacility:_ C:: _:'1_O'_YlI_ M_f'>. _______ Oate: :;:t[ \ \ 13 

S 0'J'W' t:>J.--

UnitlLocation: U"-'I 'l. - W ISWJifi''Y Performed By: __ s£'==,--______ _ 

Probe Material ___ .::S-'-"' ______ Probe Length _----'-'4s=---'~u· ' _____ _ 

Connecting Tubing Material,_Lf'J_A-____ Connecting Tubing Length, __ N4_' ___ _ 

Barometric pressure--'=L=1"'. _h_1.l.-____ ,Ambient Temperature __ l '-'1'-o ____ _ 

Test No. S-;). 5\¥-'1>~ i" <;'-2/s""-1 S . ~O<;rlb 

Vial 10 t-l/(.>, rJ IA L 

Canister 10 000 '3 2-0 <7vO sst) I 

Time Vacuum Time Vacuum Time Vacjuum 

Pre-Test Leak Start OCZ06 30" DlDO 30'i 

Check 

Pre-Test Leak Stop o~ tD 3D 1\ 01 10 )0" Check 

Sample Start 4J ){)V '3() ~ Collection OliO 6110 

I 

tJ U"\ 'J.l 'J. S II 

C)~ :n ;2 S" II 

~<X1't~ 20 , .! O(1'1tf :2.-0 V 

~ ;"0\1 \ " \. iOA. . w' I , - \':) ' / I 

Sample Stop 

(03'-{ LO lO3'1 (0 Collection I 

Post -Test Leak Start 

I{J...O(} I,) Check I / d Uc) /() 

Post-Test Leak Stop /')-./0 10 /2../U /0 

Check I 

I 

Line Rinse ;/ /' / /' Volume I 

Comments: _________________________ _ 

Date of last revision 11/13/08 

DS834043 

Master Document StoragelFormslDatasheetslField Datasheets 
SCAQMD METHOD 25.3 

EVACUATED CANISTER SAMPLING DATA 

Client/Facility: ivL~ <"--q < Date: (-,3 (). /3. 

Unit/Location: X 1/ h ,'.<, ..... / IA " ,' j i 2 Performed By:_.:::S:....:5=--______ _ 

L'" Inff Probe Material_---"..J"-.::. J _ ______ Probe Length _""--"'0'---______ _ 

Connecting Tubing Material __ 5:::.....<5'---__ Connecting Tubing Length--'!I-l .:..,f'r _ __ _ 

Barometric Pressure "J-y, 8 0 Ambient Temperature_.!..7.:.o_b 

____ _ 

Test No, .:5~ J./('- a.'C_" tO{)-,)f 6, ~J6 '(1" ... - iOD-;1§! 

Vial 10 ~ - Canister 10 Iho C' S 11 «Joo 5.31 

Time Vacuum Time Vacuum Time Vacuum 

Pre-Test Leak Start 

IOf!)~ set' ).ti,3 t' Check 1\0010 

Pre-Test Leak Stop 

10 I (; 3,j Check " /Blie ~1. § " 

Sample Start 2..'1/r 

,\,0' 2.11 N 

Collection ~ \i 0 \ / , I 

- T' tV I' / )'1.-,., 

cl126 2L{ IIlG 2 Lf: U' / 

/ 

Nfl :4,( Iq ,'J ilL!,; Iq L 

ui2.02 13)' 1202.. -fG{tf / 

Sample Stop 12-{O fo Collection f2Y! Ii> / 

Post -Test Leak Start \ 

Check / J;)...). u ( 0 /~ /0 

Post-Test Leak Stop 1l-3.) ID Check 1 / 0 p-3v 

/ 

Line Rinse 

NA- / ~ ---- V 

Volume ~ \J 

Comments: _____ __________ _ ________ _ 

Della;).. Al< 0u0I. ............ _ 

Date of last revision 11 /13/08 

DS834043 

Master Document StoragelFormslDatasheetslField Datasheets 

II 
SCAQMD METHOD 25.3 

EVACUATED CANISTER SAMPLING DATA 

Client/Facility: tye~ /h-<<- Date: I - 3 /- {-?, 

Unit/Location: 6.e,zt (4/" I U i;)... Performed By:--<;[;z:.L£I--'--_____ _ 

Probe Material __________ Probe Length _________ _ 

Connecting Tubing Material ';J..lJ I' Connecting Tubing Length ' I 

Barometri ~essure :H . {.:( Ambient Temperature /;.S' 

/ 

Test No, \ .5 - J-/5-iJ&(-I'i).ft 5 -;}./:' - uuc.-75-)13 

Vial 10 \ / 

Canister 10 \ OV() i1<o:3 000 '"10 

\ Time Vacuum Time VVacuum Time Vacuum 

Pre-Test Leak Sta\ •• Oq;h .. Check tJ?1t{J_ .:J-.C( , J- "j. f· 7 

Pre-Test Leak Stop 

Check ~'i}... d-1. }. " h5"l. ;rf,7 " 

Sample Start ~W·~ ., Z. 7. g' Collection z13, / (L(I( 

~LI3'>-

~<f 1'\35"" ,. 

I !4 =b~ 2-) 

~iS I A HS-:l 20'( 

G;; / '\ 

/ ~ 

/ ~ 

/ "-

Collection 

Sample Stt ~ Post -Test Leak ~{art '" Check / 

Post-Test Leak / Stop 

"'" Check ;' 

/ 

Line Rinse L 

Volume 

----"* Comments: /«_ ~i~ f)~ -Iv [f3i15 vet 

Dellai1 

... _-,-

Date of last revision 11 /13/08 

DS834043 

Master Document StoragelFormsl DatasheetslField Datasheets 
Atmospheric Analysis & Consulting, Inc. 

CLIENT 

PROJECT NAME 

AAC PROJECT NO. 

REPORT DATE 

Delta Air Quality Services, Inc. 

Gemma, Sentinel Unit 2 

130122 

21712013 

On February 5, 2013, Atmospheric Analysis & Consulting, Inc. received six (6) Six-Liter Summa 

Canisters for TNMNEOC analysis by SCAQMD 25.3 Modified and Fixed Gases analysis by EPA 3C. 

Upon receipt the samples were assigned unique Laboratory ID numbers as follows: 

Client ID Lab No. Initial Pressure 

(mmHg) 

S2/Stk-VOC-IOO-IA 130122-60797 453.1 

S2/Stk-VOC-I 00-1 B 130122-60798 479.1 

S2/Stk-VOC-50-IA 130122-60799 376.9 

S2/Stk-VOC-50-1B 130122-60800 416.0 

S2/Stk-VOC-75-IA 130122-60801 434.0 

S2/Stk-VOC-75-IB 130122-60802 421.4 

Upon receipt at the laboratory, the initial vacuum was recorded and the canister was pressurized to 900 

mmHg using dry UHP Helium. The PQL for this modified method was established at 0.10 ppm V (as 

Propane) as dictated by the lowest point in the calibration curve. All results were detected below this level 

and therefore reported as <PQL. 

Canister numbers from the Chain of Custody did not match those on the sample ID tags for samples 

60797-60802. The correct canister numbers were ascribed onto the original COC according to "Test #." 

I certit'y that this data is technically accurate, complete and in compliance with the terms and conditions 

of the contract. Release of the data contained in this hardcopy data package has been authorized by the 

Laboratory Director or his designee, as verified by the following signature. . 

If you have any questions or require an explanation of your data results, please contact the undersigned. 

9/4. b J 

Marcus Huep~? 

Laboratory Director 

This report consists of 41 pages. 

Page 1 

1534 Eastman Ave., Ste. A • Ventura, • CA 93003 @ www.aaclab.com. (805) 650-1 642 • FAX (805) 650-1644 
® lAce Atmospheric Analysis & Consulting, Inc, 

SAMPLE RECEIPT / LOG-IN REPORT 

AAC Project 130122 Received By: . J. Zachman 

Sample Pro i eet Desc Clients ID Matrix Sampling Sampled By Sample # 

Receipt Date Date/Time 

21512013 Delta Air Quality S21Stk -V OC-I 00 Summa 113012013 Client 60797 

1045 -IA Canister 

Gemma, Sentinel Unit 2 

21512013 Delta Air Quality S21Stk-VOC-I 00 Summa 113012013 Client 60798 

1045 -IB Canister 

Gemma, Sentinel Unit 2 

21512013 Delta Air Quality S2/Stk-VOC-50- Summa 21112013 Client 60799 

1045 IA Canister 

Gemma, Sentinel Unit 2 

21512013 Delta Air Quality S2IStk-VOC-50- Summa 21112013 Client 60800 

1045 IB Canister 

Gemma, Sentinel Unit 2 

21512013 Delta Air Quality S21Stk-VOC-75 - Summa 21112013 Client 60801 

1045 IA Canister 

Gemma, Sentinel Unit 2 

21512013 Delta Air Quality S21Stk-VOC-75- Summa 21112013 Client 60802 

1045 IB Canister 

Gemma, Sentinel Unit 2 

TURN AROUND TIME: Normal (I0days) 

Lab Due Date: 211212013 Total Samples: 

REMARKS: 

Client returned 7 x Summa canisters + 7 x Flows. Canister numbers did not match from the COC to the sample ID 

tags for samples 60797-60802. The correct canister numbers were ascribed onto the original COC according to 

TEST #. 

Page 2 

Analysis 

Requested 

SCAQMD 25.3M 

SCAQMD 25.3M 

SCAQMD 253M 

SCAQMD 253M 

SCAQMD 25.3M 

SCAQMD 25.3M 

6 
Client: 

Date: 

Delta Air Quality 

2/5/2013 

Canister # 

531 

517 

382 

483 

520 

558 

Atmospheric Analysis & Consulting, Inc 

CANISTER PRESSURE LOG 

Project No.: 130122 

Sample # Initial Pressure Final Pressure 

60797 453.1 907.7 

60798 479.1 908.0 

60799 376.9 908.6 

60800 416.0 913.0 

60801 434.0 906.7 

60802 421.4 907.1 

1 

Page 3 
~07f7 

"07~ 

&it) 7'1' 

to ()7oD 

fl." rtr> ( tof) 11":' 

Al elF (30 I t- 'l--

CHAIN OF CUSTODY 

CliENT: Sentinel r~Mt TEST DATE(S): 113012013 2/1 /2013 

LOCATION: ______ ~2 ______________________________________________________________ _ SAMPLER(S): RM 

SAMPLE LOCATION: ~S~~~ ________________________________________________________________ ___ PROJECT MANAGER: 8F '<t 

Q) 

DATE DUE: 219/2013 OJ) 

oj TEST METHOD(S): ______ --"S"'C"AQ"M=D.=2"'5."-3 ____________________________________________________ ___ 

OUTSIDE LA8 REQUIRED?: -'Y"es"-__________________________________________________________ _ COMPliANCE TEST? ~ Yes 

• 0 

1130/2013 S21S~·VOC·1 00-1A SCAQMD 25.3 Canister~ s-3; 1 RM 

1/3012013 21S~·VOC· 1 00-18 SCAQMD 25.3 Canister M9ia4 S", 1 RM 

2/1 /2013 S21S~·VOC·50·1A SCAQMD 25.3 Canlster~ '3 2- 1 RM 

2/1/2013 S2IStk·VOC·50·1 B SCAQMD 25.3 Canister #QQ866fI ,. 1 RM 

21112013 S21Slk·VOC·75·1A SCAQMD 25.3 Canister #9Qi3&2 ~-L 0 1 RM 

211/2013 S21Slk-VOC·75-1 8 SCAQMD 25.3 Can ster~ .s-s-8 1 RM 

n. u~h .. 

ala ampes 

eagent 

Keagent Lot #'S:I ~ 

,-------------------"RE"'L-oEA=SE"'D"B"'y,---------- - -- ----,--- --~ ------ ~--- "RECEIVED gy-- - -, --DATE/TIME 

_ . m o m . - - - m ?.. - 70 / '" ~ ~-'J ~i4 I r9k:jg; 6 ~~ [777&ti7f:F¥kl!! . "/~; .. ~ I 1;:;/3 ;:;~ . 

Note: Canister #000403 and #000411 WCIt: VUIUt;:\j It:;,~. rlCdl3C UU I IUI Cl I IGIY'C. - <./ 

A 
Results 

Page 5 
Atmospheric Analysis & Consulting, Inc. 

CLIENT 

PROJECT NO. 

MATRIX 

UNITS 

Client 10 

: Delta Air Quality Services, Inc. 

: 130122 

Air 

: ppmC 

Lab 10 # 

Tank Vol 

Liters 

as per 

LABORATORY ANALYSIS REPORT 

SCAQMD 25.3 Modified 

Initial Pressure 

mmHg(p;) 

Return 

Pressure 

Final 

Pressure 

PQL:: 0.10 ppm V Propane x 3.0 (carbon conversion) x Tank Dilution Factor x 1.086 (correction factor) 

EPA3C 

PQL: 0.1 % An,lvte 

Client 10 Lab 10# Oxygen CO 

S2/Stk-VOC-IOO-IA 130122-60797 13.0 <PQL 

S2IStk-VOC-IOO-I B 130122~0798 12.9 <PQL 

S2IStk-VOC-50-IA 130122~0799 14.1 <PQL 

S2lStk-VOC-50-1 B 130122-60800 14.2 <PQL 

I S2IStk-VOC-75-IA 130122-60801 13.2 <PQL 

S2IStk-VOC-75-IB 130122-60802 13.2 <POL 

Fixed Gases have been normalized to 100% on a dry weight basis 

Tank Dil 

Factor 

CO2 

5.9 

6.1 

5.3 

5.2 

6.1 

6.0 

SAMPLING DATE : 01/30, 02/0112013 

RECEIVING DATE: 02/05/2013 

ANALYSIS DATE : 0210612013 

REPORT DATE : 0210712013 

Total 

NMNEOC' PQL 

~d_~~ MarcusHuep!fe 7 . 

Laboratory Director 

Page 6 

1534 Eastman Ave., Ste. A • Ventura, • CA 93003 * (805) 650-1642 • FAX (805) 650-1644 • www.aaclab.com 
Method 25.3 Modified Calculation Summary Sheet 

TNMNEOC - CTCA x DFTank X 3.0 x 1.086 

Where: 

lNMNEOC = Gaseous concentration of Source, ppmV (as Carbon) 

CTCA = Average of analysis results from chromatograms, ppmv (as Propane) 

DFTank = Dilution factor resulting from tank pressurization upon receipt (PdP,) 

3.0 = Conversion of result (as Propane) to (as Carbon) 

Per method section 4.11, the fmal concentration includes a 1.086 bias correction factor. 

Where: 

Pr= Final canister pressure after pressurization for analysis ifrom Sample Receiving Data Sheet) 

p, = Return canister pressure upon sample receipt (from Sample Receiving Data Sheet) 

Page 7 
QA/QC 

Summary 

Page 8 
Atmospheric Analysis & Consulting, Inc. 

Quality Control/Quality Assurance Report 

I 

Date Analyzed 

Analyst 

Unit.~ 

: 02/0612013 

:ZG 

: 0/0 

I ~ ODeniru!. Continuine: Calibration Verification - SeA 

AACID I Analyte I 0 , 

Spike Cone 5. 18 

CCV Result 5.04 

% Rcc-"" 97.4 

5.3 

0, 

Concentration NO 

MD 25.1 25.3 

N, 

14.4 

15.78 

109.5 

N, 

NO 

III-Laboratory Control Spike & Du licate - SCAQMD 25.1,25.3 

AACID Analyte N, 

Sample Cone 0.0 

Spike Cone 14.4 

LCS Result 15.2 

La b Control 

LCSD Result 14.6 Standards LeS % Rec P 105.3 

LCSD % Rec" 101.4 

%RPD· ... 3.8 

IV -Sample & Sample Duplieate - SCAQMD 25.1,25.3 

AACID Analyte 0, 

Sample 6.3 

SampleDup 6.3 

130122-60797 

Mean 6.3 

%RPD "'*" 0.5 

V -Matrix Spike & Duplicate - SCA( MD25.125.3 

AACID Analyte N, 

SampleConc 19.7 

Spike Cone 9.2 

MS Result 29.7 

130122-60797 MSD Remit 29.9 

MS % Ree""" 108.3 

MSD % Rec """" 110.0 

% RPD .** 1.5 

VI - Clos~ Continuin~ Calibration Verification - SeA 

AACID 

CCV 

• Must be 85-115% 

•• MUl1 be 75-125% 

... Must be < 25% 

ND - Not Detected 

Analyte 

Spike Cone 

Result 

0/ 0 Rec 11" 

<,R,L '" less than Reporting Limit 

0, 

5.18 

4.82 

93.0 

CO, 

0.0 

10.3 

10.5 

10.2 

102.7 

99.4 

3.2 

N, 

39.4 

39.6 

39.5 

0.7 

CO, 

1.4 

10.3 

12.1 

12.2 

104.1 

104.8 

0.7 

QMD 25.1 25.3 

N, 

14.4 

15.2 

105.4 

CO, 

10.3 

10.67 

104.1 

co, 

NO 

CH, 

0.0 

9.9 

9.7 

9.4 

93.0 

94.2 

3.9 

CO, 

2.8 

2.9 

2.8 

2.6 

Cu. 

0.0 

9.9 

10.4 

10.5 

104.9 

105.5 

0.6 

CO, 

10.3 

10.5 

102.2 

Instrument ID 

Calb Date 

TCD#1 

04/13/2012 

Reporting Limit: 0.1 % 

CH, CO 

9.9 10.3 

10.02 10.45 

100.8 10 1.0 

Cu. co 

NO NO 

CO 

0.0 

10.3 

10.2 

9.8 

98.2 

94.3 

4.0 

Cu. CO 

0.0 0.0 

0.0 0.0 

0.0 0.0 

0.0 0.0 

CO 

0.0 

10.3 

10.9 

11.0 

105.5 

106.3 

0.8 

Cu. CO 

9.9 10.3 

9.8 10.2 

98.6 99.0 

4/L4 

Marcus Hueppe 

Laboratory Director 

Page 9 

1534 Eastman Ave., Ste. A • Ventura, • CA 93003 www.aaclab.com • (805) 650-1642 • FAX (805) 650-1644 
Atmospheric Analysis & Consulting, Inc. 

SCAQMD Method 25.1,3 Quality COlltrol/Quality Assurallce Report 

I 

I 

Date Analyzed 

Analyst 

02106/2013 

: ZG 

I -Open"ng I I Carb r afon I Ver"ficafo II I n Standard 

AAC II> Analyte Concentration 

O-CV NMNEOC 0.27 

O-CV dp NMNEOC 0.27 

O-CV tp NMNEOC 0.27 

" - Method Blank 

AACID I Analyt. I Resul! 

MB I NMNEOC I NO 

III - Matrix Snike & DUDlic.t. 

Sample 

AACID Analyte 

Concentration 

130102-60714 I NMNEOC II 0.00 

IV - I DDm Backflush Standards 

MCID I Analyt. I Result 

Backflush 1 NMNEOC 0.884 

Backflush 2 NMNEOC 0.950 

Backflush 3 NMNEOC 1.023 

Result 

0.262 

0.266 

0.267 

Spike 

Added 

I 54.35 

I % Recovery .... 

81.3 

87.4 

94.1 

V - Bracketed CloSing Calibration Verification Standards 

I AACID I 

C-CV Low 

C-CV High 

* Must be 90-110% 

** Must be 80-120% 

•• * Must be 75-125% 

**"'* Must be < 25% 

"''''*.* Must be < 10% 

Analyte 

NMNEOC 

NMNEOC 

I Concentration I Result 

0.27 0.261 

2.72 2.82 

% Recovery" 

96.4 

97.9 

98.3 

MS 

Result 

I 43.66 I 

I 

I % Recovery'" I 

96.0 

103.8 

MSD 

Result 

43.81 I 

Instrument 10: FIO#4 

Un its: PPMV 

Calibration Date: 

MS MSD 

0/8 Ree **'* 0/0 Ree It'" 

80.3 I 80.6 

Laboratory Director 

111012013 

% RPD ...... + 

I 0.4 

Page 10 

1534 Eastman Ave., Ste. A • Ventura, • CA 93003 www.aaclab.com • (805) 650-1642 • FAX (805) 650-1644 

I 
Atmospheric Analysis & Consulting, Inc. 

SCAQMD Method 25.1,3 Quality Control/Quality Assurance Report 

Date Analyzed : 02106/2013 

Analyst: : ZG 

Sample Duplicate analysIs I . RPD' 

I AAC !D I Result I Result Du~ 

130102-60714 <PQL <PQL 

130102-60715 <PQL <PQL 

130122-60797 <PQL <PQL 

130122-60798 <PQL <PQL 

130122-60799 <PQL <PQL 

130122-60800 <PQL <PQL 

130122-60801 <PQL <PQL 

130122-60802 <PQL <PQL 

I Quali!1 Assurance Criteria 

Cone. (ppmv) %RPD 

1-3 <20 

4-6 $15 

7-12 <12 

13-30 <10 

31-50 <5 

S 

I 

Instrument !D: F!D #4 

Units: PPMV 

Calibration Date: 111012013 

I %RPD I 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

Marcus Hueppe 

Laboratory Director 

Page 11 

1534 Eastman Ave., Ste. A • Ventura, • CA 93003 @ www.aaclab.com. (805) 650-1642 • FAX (805) 650-1644 
Raw Data 

Page 12 . 
600 

500 

400 

. 

~ " 300 

" 

~ 0 

0 200 ~ 

• 

~ 

100 

" ~ 

'g 00 

~ 0 m 

u ':i: ~ 

0 0 ::i u a 'x ~ 00 'g a 0 0 0 " a a a 

~ c ~ :; e> 

" ~ • 

~ 6 0 

e ! a M 

( " 0 

;: • I I " ';-

0 

-100 

0 2 4 6 

Sample Name = 130122-60797 

Instrument = TeO #1 

Chrom Perfect Chromatogram Report 

::i 

00 

" c 

• ~ 

au u ;0 

0 .- 0 

::i z~ 

~ 

~~ 00 0 " ;, mO 0 • '" 0 

• ~ " ~ 

• ~ ;;; 

" m " 

B 10 

130122-60797 

" ~ 

00 

" ;, 

u 

x u 'g g 0 

a a a ~ ~ 

" 0 0 0 ;, a ~ 

" " . ~ " " w ;;; 

, 

12 

Time - Minutes 

, 

14 

-< 

~ 

00 

" 

~ 

~ 

;;; 

16 18 20 22 

Raw File Name = C:\CPDATA\lnst#01\2013\020613.0006_raw Date Taken (end) = 2/6/2013 9:29:25 AM 

Method File Name = C:\Cpmethods\lnst #01\2012\D1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:\Cpmethods\lnst #01 \2012\D1945-D1946-3C-041312-standard .CAL 

Peak # Ret Time Name Amount Amt% Area Area % Type Width 

1 7.03 Oxygen-MS5A 6.302 13.001 86350 12.448 BB 0.09 

2 9.15 Nitrogen-MS5A 39.354 81.196 573552 82_684 SBB 0.11 

3 9.54 C02-Q bond 2.812 5.803 33766 4.868 TBB 0.21 

Total Area = 693668 Total Height = 99456.77 Total Amount = 48.46832 

" 

Printed on 2/6/2013 9:29:56 AM 

Page 13 

Page 1 of 1 
Chrom Perfect Chromatogram Report 

130122-60797 dp 

600 

500 

400 

. 

"0 

~ 300 « « ~ ~ 

'" u w w 

~ c 

0 200 :iT 

• 

~ 

100 

0 

c 

~ 'i: 0 ::i 00 w 0 • ~ ~ " ~ ou u u " g =c c « U 0 - 0 ::i u u 0 ~ x 0 ZD 'x D W 0 c 0 c c « g c D o W c 0 0 ~ 

':1 " 0 0 0 0 '"-: N " 0 D D W C " '" '" ~ 

~ " " 0 0 • • 0 c " « c c " " " ~ ~ 

! 0 0 M • • 0 c :ii c ~ " jii 0 ~ oS " .. • ~ • • ~ ~ 

I I U ';' " " ';' w w w 

·100 

0 2 4 6 8 10 12 14 16 18 20 22 24 

Time - Minutes 

Sample Name ; 130122-60797 dp 

Instrument = TCD #1 

Raw File Name; C:ICPDATAllnst#01120131020613.0007,raw Date Taken (end) ; 2/6/2013 9:49:02 AM 

Method File Name ; C:ICpmethodsl lnst#0112012ID1945-D1946-3C.MET Dilution Factor; 1 

Calibration File Name; C:ICpmethodsl lnst #0112012ID1945-D1946-3C-041312-standard.CAL 

Peak # Ret Time Name Amount Amt % Area Area % Type Width 

1 7.03 Oxygen-MS5A 6,332 12.960 86766 12.411 BB 0.09 

2 9.15 Nitrogen MS5A 39.640 81 .1 34 577714 82,634 SBB 0.11 

3 9.54 C02-Q bond 2.885 5.906 34641 4,955 TBB 0.20 

Total Area; 6991219 Total Height; 99790.36 Total Amount = 48.8572 

-_._------------ --------------- - --

Printed on 2/6/2013 949:25 AM 

Page 14 Page 1 of 1 
Sample Name = 130122-60798 

Instrument = TeO #1 

Raw File Name = C:tCPDATAllnst#01t2013t020613.0010.raw Date Taken (end) = 2/6/201310:49:29 AM 

Method File Name = C:tCpmethodstlnst #01 \2012tD1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:tCpmethodstlnst #01\2012tD1945-D1946-3C-041312-standard.CAL 

Peak # Ret. Time Name Amount Amt% Area Area % Type Width 

1 7.03 Oxygen-MS5A 6.916 12.947 94762 12.398 BB 0.09 

2 9.15 Nitrogen-MS5A 43.327 81.112 631446 82.617 SBB 0.1·1 

3 9.54 C02-Q bond 3.173 5.941 38100 985 TBB 0.20 

Total Area = 764307.6 Total Height = 106587 Total Amount = 53.41557 

Printed on 2/6/201310:50:47 AM 

Page 15 Page 1 of 1 
Chrom Perfect Chromatogram Report 

130122-60798 dp 

'00 

500 

400 

. 

'5 

~ 300 ,. 

~ 0 200 :t 

• '" 

100 

0 

« « ~ ~ 

-g w w 

" " « 0 C C ~ rn 

• • w 0 :;: ~ 

u ,i: " " u ~ ;, 

" ;:; 0 .- 0 " 0 'x " z~ « " u u ~ w u 0 " 0 ~ 0 " " ~ « ~o "' 0 0 ~ <1 " " " 0 0 0 0 "": N " ,. 0 ~ ~ 

:;; c "' ~ " " ;, ';"8 ;, ,. <1 <1 " • '" "' ~ ~ " " " " • • ;, 

e e 0 ~ ~ • 0 • " " '" :. 0 • £ " • • ';. ';. ~ ;; ~ • • £ £ £ ~ ~ u . ; " .,; ,. u w w w 

·100 

0 2 4 , 8 10 12 14 16 18 20 22 24 

Time - Minutes 

Sample Name = 130122-60798 dp 

Instrument = TeD #1 

Raw File Name = C:ICPDATAllnst#01120131020613.0011.raw Date Taken (end) = 2/6/2013 11 :08:12 AM 

Method File Name = C:ICpmethods\lnst #01\2012\D1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:\Cpmethods\lnst #01 \2012\D1945-D1946-3C-041312-standard.CAL 

Peak # Ret Time Name Amount Amt% Area Area % Type Width 

1 7.03 OXYgen-MS5A 6.498 12.904 89036 12.362 BB 0.09 

2 9.15 Nitrogen-MS5A 40.746 80.91 7 593828 82.450 SBB 0.11 

3 9.54 C02-Q bond 3.112 6.180 37360 5.187 TBB 0.20 

Total Area = 720224.1 Total Height = 101784.8 Total Amount = 50.35493 

Printed on 2/6/2013 11 : 13:05 AM 

Page 16 Page 1 of 1 
SC(h 

I 

J 

I 

500 -j 

~ 400 

" 

~ 300 

" ~ 

c 

~ 0 

m c C! 0 

I ~ ~ • 

• "' ~ 

0 ~ , ~ n w 0 

C! ~ ~ c 0 0 

100 c ., • • 

~ ~ 0 " c 

e e 

'" ~ 01 f ;>. 

I j\ U 

,roC 

o 2 4 6 

Sample Name = 130122-60799 

Instrument = TCD #1 

Chrom Perfect Chromatogram Report 

c 

• ;: 

o ~ o 

n 

o 

* M • o ;; 

• ' {I !' " 

8 

« 

~ 

w 

" c 

• 

~~ 

~g « z n ~ 

~C! w ~N 

",0 " * u 

~ ~ • 

'" " I I 

10 

130122-60799 

« 

~ 

w 

" 

~ • ., ~ ~ 

0 c c c 0 0 

0 n n 

" C! C! c 

0 ~ ~ € • • • ~ ~ 

u W W 

12 14 

Time - Minutes 

;:l 

w 

" 

~ • ;; 

w 

16 18 20 22 

Raw File Name = C:ICPDATAllnst#01120131020613.0012.RAW Date Taken (end) = 21612013 11:30:17 AM 

Method File Name = C ICpmethodsllnst #01\2012ID1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #01 \2012ID1945-D1946-3C-041312-standard.CAL 

Peak # Ret Time Name Amount Amt % Area Area % Type Width 

1 7.03 Oxygen-MS5A 5.579 14.128 76448 13.523 BB 0.09 

2 9.17 Nitrogen-MS5A 31 .828 80.600 463869 82.055 SBB 0.10 

3 9.56 C02-Q bond 2082 5.273 24999 4.422 TBB 0.22 

Total Area = 5653 16.3 Total Height = 85716.88 Total Amount = 39.4896 

24 

Printed on 216/2013 11 :3048 AM 

Page 17 Page 1 of 1 
Chrom Perfect Chromatogram Report 

130122-60799 dp 

600 

500 

400 J 

" " " 300 ::'i i « u w ~ 

0 ,. w « ~ 0 " " ~ '" " w 0 '? • • " 0 200 :;! ~u ;, ~ ~ • .; u 00 

::; u =0 u • 0 'K e z.o .. 'K u u ~ D W g 0 ~ g e e .. ~ e D 

~'? w 0 0 ~ 

~ ~ 0 0 0 '? " 0 D D W 

" " '" _ N 

~ " 0 0 " 100 . • .. • 

~~ ~ ~ ;, ;, ;, 0 e e e 

e 0 

~ M • • 0 e e e 

i '" " ~ ~ D u ;; ;; ~ ~ ~ " ~ 

I I ;) 0;- w w W ,7' ,. u 

0 

-100 i--~ ___ -, __ -, __ -r __ '-____ -' __ ~ __ '-, __ ~-' __ ~ __ '-~ ___ '-,~ ___ r-, ____ -r __ ~ __ r-____ ~ o 2 4 6 8 10 12 14 16 18 20 22 24 

Time - Minutes 

Sample Name = 130122-60799 dp 

Instrument = TC D #1 

Raw File Name = C;tCPDATAtJnst#01t2013t020613.0013.raw Date Taken (end) = 2/6/2013 11 :47: 1 0 AM 

Method File Name = C:tCpmethodstlnst#0112012tD1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:tCpmethodstlnst #0112012t01945-0 1946-3C-041312-standard.CAL 

Peak # Ret. Time Name Amount Amt % Area Area % Type Widih 

1 7.03 Oxygen-MS5A 5_512 14.169 75529 13.566 BB 0_09 

2 9.17 Nitrogen-MS5A 31.293 80.444 456068 81.915 SBB 0.10 

3 9.55 C02-Q bond 2.096 5.387 25159 4.519 TBB 0_23 

Total Area = 556756.8 Total Height = 84950.39 Total Amount = 38.90063 

-------- - ------------------------------

Pnnted on 2/6/2013 1147:42 AM 

Page 18 

Page 1 of 1 
Chrom Perfect Chromatogram Report 

130122-60800 

600 

500 

400 

"0 

i§ 300 

" 

w 

0 

0 200 ~ u 

w 0 

0 " D 

Ci 

100 0 

w 

~ 

0 

~ I 

0 

'" '" ~ ~ u ~ ~ 0 'J; ~ '" 0 ~ 

m ~ 

0 w w " .i: ~ ~u .i: x u eo 

'" 0 . ..: 0 ~ " 0 ZD '" , " " ~ 0 0 ~ 0 '" " c C D vCi W c 0 0 ~ " 0 0 0 0 " 0 D D ~ 

C " ~N 

" " " ";0 " " 0 ':i: " w 0 c -< c 

~,~ :;; c ~ * ~ 

0 0 M 1 0 c 

~ " 0 ~ " w 1 . '" J .. .. . I " " ':- " " u w W w 

·100 I 

-- -,-- , 0 2 4 6 8 10 12 14 16 18 20 22 24 

Time - Minutes 

Sample Name c 130122-60800 

Instrument = TCD #1 

Raw File Name c C:ICPDATAllnst#01120131020613.0014.raw Date Taken (end) c 2/6/201312:05:14 PM 

Method File Name c C:ICpmethodsllnst #01\2012ID1945-D1946-3C.MET Dilution Factor c 1 

Calibration File Name c C:ICpmethodsllnst #01 \2012ID1945-D1946-3C-041312-standard.CAL 

Peak # Ret. Time Name Amount Amt % Area Area % Type Width 

1 7.03 Oxygen-MS5A 6.106 14.262 83668 13.648 BB 0.09 

2 9.16 Nitrogen-MS5A 34.537 80.672 503345 82.105 BV 0.1 1 

3 9.55 C02-Q bond 2.169 5.066 26039 4.247 VB 0.23 

Total Area c 613053 Total Height c 91169.8 Total Amount c 42.81182 

Printed on 2/6/201312:2034 PM Page 1 of 1 
600J 

500 

400 -

. 

'ii 

~ 300 « 

" ~ 

~ 0 '" ~ " C '" 0 9 ~ 0 200 ~ ~ • 

• 0 :'i ~ 0 0 ;< 

'" D '" g ~ c 

:! " 0 0 0 

~ ~ 

100 "' " ;; • 

~ ~ 0 c 

e e 0 • '" " 0 '<- '<- . I I 0 .. 0 

-100 

o 2 4 6 

Sample Name = 130122-60800 tp 

Instrument = TeO #1 

Chrom Perfect Chromatogram Report 

130122-608001p 

:'i 

'" '" « 

~ c 

• '" ~ eo 

~~ ~ ."= 0 ~ 0 ZD « ;< ~ 

0 ~ ~ g c D ~"1 '" ~ 0 

9 " 0 D -N 

~ ";0 ;, " 0 0 ;, ;, 

~~ :; 0 

• 0 0 

~ ~ " " • " • • " " " 0 w W 

8 10 12 14 

Time - Minutes 

, 

16 18 20 22 

Raw File Name = C:ICPDATAl lnst#01\20131020613.0016.raw Date Taken (end) = 21612013 12:37:39 PM 

Method File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C-041312-standard .CAL 

Peak # Ret. Time Name Amount Amt% Area Area % Type Width 

1 7.04 Oxygen-MS5A 5.934 14.195 81319 13.590 BB 0.09 

2 9.1 7 Nitrogen-MS5A 33.622 80.420 490006 81.892 SBB 0.10 

3 9.55 C02-Q bond 2.251 5.385 27031 4.5t8 TBB 0.23 

Total Area = 598355.5 Total Height = 89400.6 Total Amount = 41.80766 

24 

Printed on 21612013 12:37:57 PM Page 1 of 1 

Page 20 

l>H ~~)13 
Chrom Perfect Chromatogram Report 

130122-60801 dp 

600 

500 1 , 

' 00 

" i§ 300 

" -< -< ~ ~ 

~ w w 

~ 0 

0 200 :;} 

• 

~ 

100 

0 

0 " ~ -< 0 c ~ m w 

'" • • " ;>: ~ 

-g • o~ " -< ~ C; ~ 

-= :5 ~ 

0 ~ x 0 z~ -< -x ~ ~ 

~ w ~ 0 0 ~ 0 c c -< 

" c 0 0 ~ wO w 0 0 0 ~ '" 0 0 g, 0 ~N 1: 0 ~ ~ w c C " " :c< " ~o " '" 0 • 

~ • ~ 0 0 c c c ~ " 

~ u 0 ~ e 0 M • • 0 

i '" iii 0 ~ 

/\ ; ~ fii • • • "- ~ 

I I U ,; " " " " " " " u w w w 

-1 00 

0 , 6 8 10 12 " 16 18 20 22 

Time - Minutes " 

Sample Name = 130122-60801 dp 

Instrument = TeD #1 

Raw File Name = C;ICPDATAllnst#01120131020613.0018.raw Date Taken (end) = 2/6/20131:19:52 PM 

Method File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C-041312-standard.CAL 

Peak # Ret. Time Name Amount Amt% Area Area % Type Width 

1 7.03 Oxygen-MS5A 6.046 13.179 82849 12.627 BB 0_09 

2 9.16 Nitrogen-MS5A 37.023 80.700 539579 82.235 SBB 0.11 

3 9.54 C02-Q bond 2.808 6.121 33715 5.138 TBB 0.21 

Total Area = 656143.1 Total Height = 95167.28 Total Amount = 45.87751 

Printed on 2/6/2013 1 :20: 18 PM Page 1 of 1 

Page 21 
Chrom Perfect Chromatogram Report 

130122.00801 tp 

600 

500 

400j . 

.. 

~ 300 ,. « « ~ ~ 

~ '" '" ~ c 

0 200 ~ ~ 

• c 

0 ~ D 

0 

'00 ~ g' 

i 

r 

c ,. " « 0 C C ~ m '" 9 • • ~ " ~ 

• o~ .. « ~ .5 ~ ~:5 ~ 

~ C ZD « x ~ ~ 

0 0 ~ c c « '" ~ C D ~O '" g 0 0 ~ " c c 0 0 0 9 --:..:. " 0 D D '" ~ D " '" ~o * " 9 9 ,. 

" « • 

* c C U c • ~ e 0 M • • 0 c 

" D 0 £ ~ £ " ~ • ~ • " • ~ • • ~ £ r: u ';" " ~ " u W W w 

a 

,'00 

r 

a 4 6 a 10 12 14 16 18 20 22 " Time - MirlJtes 

Sample Name = 130122·60801 tp 

Instrument = TCD #1 

Raw File Name = C:ICPDATA\lnst#01120131020613.0019.raw Date Taken (end) = 2/6/20131:37: 16 PM 

Method File Name = CICpmethodsllnst #0112012ID1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C-041 31 2-standard.CAL 

Peak # Ret. Time Name Amount Amt% Area Area % Type Width 

1 7.03 Oxygen-MS5A 6.130 13.207 84003 12.651 BB 0.09 

2 9.16 Nitrogen-MS5A 37.510 80.812 546667 82.330 SBB 0.1 1 

3 9.54 C02-Q bond 2.776 5.981 33328 5.019 TBB 0.21 

Total Area = 663998.2 Total Height = 96125.48 Total Amount = 46.41586 

Printed on 2/6/2013 1:38:05 PM Page 1 of 1 

Page 22 
600 

500 

400 

. 

'5 

~ 300 ,. 

~ 

u "" ~ 

m 0 

0 'i' m 0 

0 

0 100 ~ 

• '" 

100 

0 • 

;, ~ ~ .5 "" u 0 ~ ·x ~ m u 0 

0 0 0 

9 " 0 0 0 '" 0 C 

• • 0 "' " 0 "" ~ ~ 

0 0 0 M 

i i " ~ 0 :. I I U ';-

0 

·100 

0 1 4 6 

Sample Name = 130122·60802 

Instrument = TCD #1 

Chrom Perfect Chromatogram Report 

"" ~ 

m 

'" C 

• 

~u 

e o ~ :::: 0 "" 0 z~ ~ 

~ ~"1 m 

9 - . N 

• ~o " ;, 0 

~~ :; ~ • ~ 

;;; ;;; 

" " 

8 10 

130122-60602 

"" ~ 

m 

,. 

;, 

u 

·x 

0 ~ ~ 0 0 0 

0 ~ ~ 

" 0 0 ;, ':i: 0 0 0 ~ • • :. ~ ~ 

U ;;; ;;; 

11 

Time· Minutes 

14 

"" ~ 

m 

" ;, 

0 

~ 

;;; 

16 18 10 11 

Raw File Name = C:ICPDATAl lnst#01120131020613.0020.raw Date Taken (end) = 2/6/2013 2:01 :52 PM 

Method File Name = C:ICpmethodsllnst #0112012ID1945·DI946·3C.MET Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0112012ID1 945-D1946-3C-041312-standard.CAL 

Peak # Ret Time Name Amount Amt % Area Area % Type Width 

1 7.03 Oxygen-MS5A 5.743 13.160 78692 12.606 BB 0.09 

2 9.16 Nitrogen-MS5A 35.276 80.839 514114 82.358 SBB 0.11 

3 9.54 C02-Q bond 2.618 6.000 31436 5.036 TBB 0.21 

Total Area = 624242.4 Total Height = 92045.65 Total Amount = 43.637,08 

14 

Printed on 2/6/2013 2:02:19 PM Page 1 of 1 

Page 23 
600 

500 

400 

"0 

;§ 300 

" "" ~ 

U "' ~ c 

0 200 ~ 

• 

~ 

100 

c ;:: 0 

'" a • 

~ U " C "" u <5 0 ~ ·x ~ "' U 0 

c c 

~ " c 0 0 c 0 

. • " '" 'i "" ~ ~ a c 0 ! 0 M 

i " ~ 0 

I I U ~ 

0 

·100 

0 4 6 

Sample Name = 130122-60802 dp 

Instrument;: TCD #1 

Chrom Perfect Chromatogram Report 

:ii 

"' " c 

• 

~ 

OU 

~ :~ g "" 0 Z~ ~ 

~ "'''I "' "I " 'eN 

" • ~o 

c 

~ ~ ~ 

" " " 

8 10 

130122-60802 dp 

"" ~ 

"' " " U 

0 

X ~ ~ c 0 0 

0 ~ ~ 

" a a 

* * c 

0 

~ • • " " u w w 

12 

Time· Minutes 

14 

:ii 

"' " . 

c 

~ 

W 

16 18 20 22 

Raw File Name = C:ICPDATAllnst#01120131020613.0021.raw Date Taken (end) = 2/6/2013 2:18:22 PM 

Method File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C.MET Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0112012ID1945-D1946-3C-041312-slandard .CAL 

Peak # Ret. Time Name Amount Amt% Area Area % Type Width 

1 7.03 Oxygen-MS5A 5.832 13.176 79918 12.621 BB 0.09 

2 9.16 Nitrogen-MS5A 35.781 80.836 521467 82.354 SBB 0.11 

3 9.54 C02-Q bond 2.650 5.988 31819 5.025 TBB 0:21 

Tolal Area = 633204.3 Total Height = 92977.34 Total Amount = 44:26297 

24 

Printed on 2/6/2013 2: 18:49 PM Page 1 of 1 

Page 24 
Chrom Perfect Chromatogram Report 

-----~---------- -------~-------~---- -----

130 122-60797 

1600 ,---------------~-------------------------------------------------------------. 

1400 

1200 

1000 

. 

"0 

~ 800 " 

~ c 

0 600 ~ 

• 

~ 

400 

0.0 10 

.

u 

, 

o 

<5 

2.0 

Sample Name = 130122-60797 

Instrument = FID #4 

3.0 

• C 

• ;; 

w 

4.0 

• C 

~ 

w ..A~ 

5.0 

Time - Minutes 

N 

U 

0 

w 

Z 

" Z 

U 

0 

w 

z 

" Z 

ro 

M 

W 

~ 

N 

W 

6.0 7.0 B.O 9.0 

Raw File Name = C:\CPDATA\lnst#04\2013\020613.0014.raw Dale Taken (end) = 2/6/201310:31:34 AM 

Melhod File Name = C:\Cpmethods\lnst #04\2013\Method25.1.3_low.mel Dilution Factor = 1 

Calibration File Name = C:\Cpmethods\lnst #04\2013\M25.1.310w-011 013.CAL 

Peak # Ret. Time Name Amount Amt % Area Area % Type Width 

1 1.88 Carbon Dioxide 1933.222 99.992 39723784 99.980 BB 0.48 

2 6.27 NMNEOC 1 0.109 0.006 5822 0~0 5 BB N 0.38 

3 6.38 NMNEOC 2 + 0.038 0.002 2053 0.005 BB 0.18 

0 .\47 

Total Area = 3.973166E+07 Total Height = 1058976 Total Amount = 1933.369 

Printed on 2/6/2013 10:33:04 AM Page 1 of 1 

Page 25 
1600 

1400 

1200 

1000 

'" ,; 

,. 

~ 800 

~ 0 

0 600 .. 

• "' 

400 

200 

0 

0.0 

~ • 

'x 

0 

0 

0 

" 0 • 0 0 

€ 

• ~ u " 

, 

62 

1.0 

~ • 

'x 

o 

o 

o 

o 

:l 

u 

,---' 

2.0 

Sample Name = 130122-60797 dp 

Instrument = FID #4 

Chrom Perfect Chromatogram Report 

• 0 

:; • 

w 

, 3.0 4.0 

130122-60797 dp 

~ 

~ 

W J. 

5.0 

Time· Minutes 

0 " 

w 

Z 

" z 

~ 

~ 

~ 

6.0 

N 

" 0 

w 

Z 

,. 

z 

~ 

w 

w 

7.0 8.0 9.0 

Raw File Name = C;ICPDATAllnst#04120131020613.0015.raw Date Taken (end) = 2/6/201310:48:24 AM 

Method File Name = C:ICpmethodsl lnst #0412013IMethod25.1 ,3Jow.met Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0412013IM25.1 ,310w-01 1 013.CAL 

Peak# Ret. Time Name Amount Amt % Area Area % Type Width 

1 1.93 Carbon Dioxide 1966.198 99.992 40401380 99.978 BB 0048 

2 5.88 NMNEOC 1 0.131 0.007 7022 0.017 BB N 0.26 

3 6.68 NMNEOC 2 ~ 0.033 0.002 1779 0.004 BB N 0.13 

0 ·\ ,=,4-

Total Area = 4.041018E+07 Total Height = 1062244 Total Amount = 1966.363 

Printed on 2/6/201310:50:22 AM Page 1 of 1 

Page 26 
1600 

14CO 

12CO 

1000 

. 

" 

~ 8CO " 

~ 

-

0 

~ 600 

• 

~ 

" Xl 

2CO 

0 

00 10 20 

Sample Name - 130122-60798 

Instrument = FID #4 

Chrom Perfect Chromatogram Report 

3.0 4.0 

130122-60798 

• -• ;;; 

W 

5.0 

Time - Minutes 

" 0 

w 

z 

" z 

M 

~ 

~ 

6.0 

0 " w 

z 

" z 

~ 

N 

.,; 

7.0 8.0 9.0 

Raw File Name - C:\CPDATA\lnst#04\2013\020613.0016.raw Date Taken (end) - 2/6/2013 11 :03:54 AM 

Method File Name = C:\Cpmethods\lnst #04\2013\Method25.1 ,3_tow.met Dilution Factor = 1 

Calibration File Name - C:\Cpmethods\lnst #04\2013\M25.1 ,310w-011 013.CAL 

Peak # Ret. Time Name Amount Amt% Area Area % Type Width 

1 1.91 Carbon Dioxide 2005.571 99.996 41210404 99.990 BB 0.50 

2 5.53 NMNEOC 1 0.050 0.002 2682 0.007 BBN 0.13 

3 6.25 NMNEOC 2 + 0.024 0.001 1282 0.003 BB 0.18 o .c;i4 

Total Area - 4.121436E+07 Total Height - 1062543 Total Amount - 2005.645 

Printed on 2/6/201311:12:56AM Page 1 of 1 

Page 27 
1600 . 

~ 

x 

0 

6 

1400 c 

0 

D 

" U 

1200 N 

~ 

-

1000 

~ , 

" 

~ 800 " 

~ c 

0 600 

~ ~ 

~ • 

400 x 

0 

c 

0 

" c • c 

200 0 

., ~ • 

• " U 

, " 

a ~ 

0 ,,-

0.0 10 2.0 

Sample Name = 130122·60798 dp 

Instrument = FlO #4 

Chrom Perfect Chromatogram Report 

• • " w 

3.0 4.0 

130122-60798 dp 

c • 

~ 

W 

5.0 

Time - Minutes 

u -

0 

w 

z 

" z 

M 

~ 

~ 

6.0 

. 

N 

u 

0 

w 

z 

" z 

~ 

w 

7.0 8.0 90 

Raw File Name = C:ICPDATAllnst#04120131020613.0017.raw Date Taken (end) = 2/6/201311:18:01 AM 

Method File Name = C:ICpmethodsllnst #04\2013IMethod25.1 ,3_low.met Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #04\2013IM25.1 ,310w·011 onCAl 

Peak # Ret Time Name Amount Amt% Area Area % Type Width 

1 1.82 Carbon Dioxide 1996.489 99.997 41023792 99.991 BB 0.49 

2 5.53 NMNEOC 1 0.051 0.003 2713 0.007 BB 0.13 

3 6.26 NMNEOC 2 .,0.019 0.001 1007 0.002 BB 0.17 

()-Ci 0 

Total Area = 4.102751 E+07 Total Height = 1060476 Total Amount = 1996.559 

Printed on 2/6/2013 11 :22:40 AM Page 1 of 1 

Page 28 
1600 

1400 

1200 

1000 

" 

~ 800 " 

· · 

_ 

0 600 :;; 

~ · 

400 

200 

a 

0.0 

• 

~ 0 

:; 

" _ • 0 

_ 

" 1 

• ;; u " .......... 

0< 

1.0 

. 

~ 

.;; 

Q 

o 

_ 

o 

~ U 

,-' 

2.0 

Sample Name; 130122-60799 dp 

Instrument = FlO #4 

Chrom Perfect Chromatogram Report 

. 

• " w 

30 4.0 

130122-60799 dp 

• 

_ 

• " w -'t, 

5 0 

Time - MinU1es 

6.0 

u 

0 

W N 

Z U " 0 z w ~ z 

• " .; z 

, 

7.0 8.0 9.0 

Raw File Name; C:ICPDATAllnst#04120131020613.0021.raw Date Taken (end); 2/6/2013 12:43:52 PM 

Melhod File Name; C:ICpmethodsl lnsl#0412013IMethod25.1,3Jow.met Dilution Faclor ; 1 

Calibration File Name; C:ICpmelhods\lnst #0412013IM25.1,310w-011 013.CAL 

Peak # 

1 

2 

Ret. Time Name 

1.89 Carbon Dioxide 

6.45 NMNEOC 1 

Total Area; 3.594645E+07 

Printed on 2/6/2013 1 :01 :34 PM 

Amount 

1749.361 

0.012 

Amt % 

99.999 

0.001 

Total Height; 1060724 

Area 

35945804 

645 

Area % 

99.998 

0.002 

Type 

BB 

BB 

Width 

0.43 

0.13 

Tolal Amount; 1749.373 

Page 1 of 1 

~~1"' 13 
. 

55 

-

'" 

~ c 

0 

~ 

• 

~ 

1600 ., .... 

1400 

1200 

1000 

' 'Xl -

600 

~ • 

400 x 

g 

0 

" c • c 200 0 • " • " • U '" ;r--:;. 

o J -;;~ 

~-- ~. 

00 " 

~ • 

·x 

.2 

o 

2.0 

Sample Name = 130122-60799 tp 

Instrument:: FlO #4 

Chrom Perfect Chromatogram Report 

• c 

• " W 

3.0 4.0 

130122-60799 tp 

• c 

. 

" W 

5.0 

Time - Minutes 

• 

6.0 

u 

0 

W N 

Z U '" 0 z w 

N Z 

M 

<D " z 

7.0 8.0 9.0 

Raw File Name = C:\CPDATA\lnst#04\2013\020613.0022.raw 

Method File Name = C:\Cpmethods\lnst #04\2013\Method25.1 ,3_low.met 

Calibration File Name :: C:\Cpmethods\lnst #04\2013\M2S.1 ,3Iow-011013.CAL 

Date Taken (end) = 2/6/201312:57 :10 PM 

Dilution Factor = 1 

Peak # 

1 

2 

Ret. Time Name 

1.82 Carbon Dioxide 

6.32 NMNEOC 1 

Total Area = 3.636246E+07 

Printed on 2/6/2013 1 :01 :28 PM 

Amount 

1769.601 

0.014 

Amt% 

99.999 

0.001 

Total Height = 1063320 

Area 

36361712 

745 

Area % 

99.998 

0.002 

Type 

SS 

SS 

Width 

0.43 

0.20 

Total Amount = 1769.615 

Page 1 of 1 

Page 30 
"

'~00 r 

! 1200 

1000 

· 

@ " 

800 " 

· c 

0 600 :;t 

~ · 

400 J I 

200 

0 

DO 

. 

u 

x 

g 

0 

" c • c 0 

~ " . " ~ 

L> " 

0, 

10 

• 

. ~ 

o 

i5 

c 

o 

~ 

:;; 

L> 

2.0 

Sample Name = 130122-60800 

Instrument :;: FlO #4 

Chrom Perfect Chromatogram Report 

~ 

~ 

i'U 

3.0 4.0 

130122-60800 

• c 

~ 

i'U 

5.0 

Time · Minutes 

, 

L> 

0 

W 

Z 

" z 

M 

~ 

':' 

6.0 

N 

L> 

0 

w 

Z 

" z 

7.0 8.0 9.0 

Raw File Name = C;\CPDATA\lnst#04\2013\020613.0023.raw Date Taken (end) = 2/6/2013 1: 15:05 PM 

Method File Name:;: C:\Cpmethods\lnst #04\2013\Method2S.1 ,3_low.met Dilution Factor = 1 

Calibra tion File Name = C:\Cpmethods\lnst #04\2013\M25.1.310w-011 013.CAL 

Peak # 

1 

2 

Ret. Time 

1.89 

5.53 

Name 

Carbon Dioxide 

NMNEOC 1 

Total Area = 3.756472E+07 

Printed on 2/612013 1 :30:24 PM 

Amount 

1828.043 

0.040 

Amt % 

99.998 

0.002 

Total Height = 1064896 

Area 

37562568 

2148 

Area % 

99.994 

0.006 

Type 

BB 

BB N 

Width 

0,45 

0.1 2 

Total Amount = 1828083 

Page 1 of 1 

Page 31 
1600 

1400 

1200 

1000 

. 

'" ~ 600 ::; 

~ < 

0 600 ~ 

• <r 

400 

200 

0 

0.0 

u • 

;< 

g 

0 

::; 

< . 0 

D :i 

" ~ 

" ;;; 

" 

:...-.,--' 

0 , 

1.0 

< 

o 

" . 

" 

~ 

ro 

2.0 

Sample Name < 130122-60800 dp 

Instrument = FlO #4 

Chrom Perfect Chromatogram Report 

• < 

• '" W 

3.0 4.0 

130122-60800 dp 

~ 

• '" w 

5.0 

Time - Miootes 

" 0 

W 

Z 

:;; 

z 

M 

~ 

, ':' 

6.0 

N 

U 

0 

w 

Z 

~ '" 

7.0 8.0 9.0 

Raw File Name < C:ICPDATAl lnst#041201 31020613.0024.raw Date Taken (end) < 2/6/20131 :28 :1 7 PM 

Method File Name = C:ICpmethodsllnst #0412013IMethod25.1 ,3_low.met Dilution Factor < 1 

Calibration File Name < C:ICpmethodsl lnst #04120 13IM25.1 ,3Iow-011 013.CAL 

Peak# 

1 

2 

Ret. Time Name 

1.85 Carbon Dioxide 

5.53 NMNEOC 1 

Total Area < 3.70025E+07 

Printed on 2/6/20131 :30:31 PM 

Amount 

1800.686 

0.038 

Amt% 

99.998 

0.002 

Total Height < 1057271 

Area 

37000440 

2059 

Area % 

99.994 

0.006 

Type 

BB 

BB N 

Width 

0.45 

0.1 2 

Total Amount < 1800.725 

Page 1 of 1 

Page 32 
1600 

1400 

1200 

~OClOj 

." 

~ 800 " 

~ 0 800 : 

'" 

400 

200 ~ 0 

00 

u • 

• 0 

c 

0 

" c • c 0 

~ • " " u • " 

'--;' 

0,,-

1.0 

u • 

. 

o 

o 

c 

o 

~ 

" u 

N 

.. 

2.0 

Sample Name = 130122-60801 

Instrument = Fl O #4 

Chrom Perfect Chromatogram Report 

• c 

• " w 

3.0 4.0 

130122-60801 

• c 

~ • 

W Ji. 

5.0 

Time - Minutes 

6.0 

u 

0 

W N 

Z U '" 0 Z w 

v Z 

v 

<6 " z 

7.0 8.0 9.0 

Raw File Name = C:ICPDATAllnst#04120131020613.0025.raw Date Taken (end) = 2/6/2013 2:30:10 PM 

Method File Name = C:ICpmethodsl lnst #0412013IMethod25.1.3Jow.met Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #04120131M25.1.310w-011 013.CAL 

Peak# 

1 

2 

Ret. Time Name 

1.82 Carbon Dioxide 

6.44 NMNEOC 1 

Total Area = 3.878849E+07 

Printed on 2/6/2013 2:45:46 PM 

Amount 

1887.675 

0.01 1 

Amt% 

99.999 

0.001 

Total Height = 1061373 

Area 

38787880 

606 

Area % 

99.998 

0.002 

Type 

BB 

BB 

Width 

0.47 

0.16 

Total Amount = 1887.686 

Page 1 of 1 

Page 33 
1600 

1400 

1200 

1000 

" .. 

§ 800 " 

: 

0 

0 600 :;, 

• 

~ 

400 

200 

0 

0.0 

~ • 

" 0 

" 0 

" 0 • 0 :ii ~ 

• " • u " 

c,----' 

Oz. 

1.0 

~ • 

." .2 

o 

" o 

~ 

• u 

2.0 

Sample Name = 130122-60801 dp 

Instrument = FlO #4 

Chrom Perfect Chromatogram Report 

• 0 

• " w 

3.0 4.0 

130122-00801 dp 

• 0 

~ 

W 

5.0 

Time· Minutes 

6.0 

u 

0 

W N 

Z U " 0 z w v Z 

M 

<D " z 

7.0 8.0 90 

Raw File Name = C;ICPDATAl lnst#04120131020613.0026.raw Date Taken (end) = 2/6/2013 2:43:32 PM 

Method File Name = C:ICpmethodsllnst #0412013IMethod25.1,3Jow.met Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0412013IM25.1 ,310w-01 1 013.CAL 

Peak # 

1 

2 

Ret. Time Name 

1.83 Carbon Dioxide 

6.34 NMNEOC 1 

Total Area = 3.90983E+07 

Printed on 2/6/20 13 2:45:52 PM 

Amount 

1902.741 

0.D16 

Amt% 

99.999 

0.001 

Total Height = 1063180 

Area 

39097468 

835 

Area % 

99.998 

0.002 

Type 

BB 

BB 

Width 

0.47 

0.17 

Total Amount = 1902.757 

Page 1 of 1 

Page 34 
1600 

1400 

1200 

1000 

;; · 

,. 

~ BOO 

~ 

• 0 600 :;-

• '" 

400 

200 

0 

0.0 

u • 

" 0 

• 0 

" ~ 0 • • " ~ 

· '" u " 

Oz. 

1.0 

~ 

" o 

is 

. 

o 

D 

" U 

2.0 

Sample Name = 130122-60802 

Instrument = FID #4 

Chrom Perfect Chromatogram Report 

• • 

~ • 

W 

3.0 4.0 

130122-60802 

• • • ;; 

W 

5.0 

Time · Minutes 

6.0 

u 

0 

w 

Z U '" 0 z w N Z 

M 

~ '" ~ 

7.0 8.0 9.0 

Raw File Name = C:ICPDATAl lnst#04120131020613.0027.raw Date Taken (end) = 2/6/2013 2:57:07 PM 

Method File Name = C:ICpmethodsllnst#0412013IMethod25.1.3Jow.met Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #0412013IM25.1 ,310w-011 013.CAL 

Peak # 

1 

2 

Ret. Time Name 

1.85 Carbon Dioxide 

6.32 NMNEOC 1 

Total Area = 3.900964E+07 

Printed on 2/6/2013 3: 13.49 PM 

Amount 

1898.428 

0.015 

Amt% 

99.999 

0.001 

Total Height = 1064429 

Area 

39008840 

800 

Area % 

99.998 

0.002 

Type 

SS 

SS 

Width 

0.47 

0.19 

Total Amount = 1898.443 

Page 1 of 1 

Page 35 
. 

" 

~ 

" 

~ 0 

~ 

• '" 

1600 

1400 

1200 

1000 

800 

600 

. 

u 400 ;; 

g 

0 

" . c c 200 0 • " ~ 

J ;;; 

" 0 :::.,.-' 

OL ~. ~-, 

00 1.0 

u • 

;; 

o 

6 

c 

o 

::; 

U 

N 

m 

2.0 

Sample Name = 130122-60802 dp 

Instrument = FlO #4 

Chrom Perfect Chromatogram Report 

• c 

• " W 

3.0 4.0 

130122-60802 dp 

. 

c 

• '" w 

5.0 

Time - Minutes 

6.0 

u 

0 

W N Z U " 0 z w N Z 

M " ':' z 

7.0 8.0 9.0 

Raw File Name = C;ICPDATAllnst#04120131020613.0028.raw Date Taken (end) = 2/6/2013 3:10:23 PM 

Method File Name = C:ICpmethodsllns1 #04\20 13IMethod2S.1 .3_lowmet Dilution Factor = 1 

Calibration File Name = C:ICpmethodsllnst #04\2013IM25.1.310w-011 013.CAL 

Peak # 

1 

2 

Ret. Time Name 

1.92 Carbon Dioxide 

6.32 NMNEOC 1 

Total Area = 3.900016E+07 

Printed on 2/6/2013 3:1 3:55 PM 

Amount 

1897.969 

0.014 

Amt% 

99.999 

0.001 

Total Height = 1064700 

Area 

38999400 

758 

Area % 

99.998 

0.002 

Type 

BB 

BB 

Width 

0.47 

0. 18 

Total Amount = 1897.983 

Page 1 of 1 

Page 36 
Calibration 

Summary 

Page 37 
SCAQMD Method 25.1 125.3 Calibration Curve (GC/FID/TCA #4) 

ANALYTE: TNMNEOC (as Propane) Analysis Date: 1/1012013 

Theoretical 

Retention time Response RPDfrom Std Theoretical 

Concentration initial result Concentration 

(ppmv) (min) Area (+1- 20%) Deviation (ppmv) 

0.11 6.89 6436 

0.11 6.84 6635 3.0 140.71 0.11 

0.27 6.85 14293 

0.27 6.86 14463 1.3 134.35 0.27 

0.54 6.86 26743 

0.54 6.85 28478 6.3 1226.83 0.54 

1.09 6.85 62346 

1.09 6.85 65692 5.2 2365.98 1.09 

2.72 6.84 167066 

2.72 6.85 158327 5.4 6179.41 2.72 

5.44 6.84 282757 

5.44 6.84 280611 0.8 1517.45 5.44 

AvgRT 6.85 RTWindow +/- 0.20 min 

Calibration Verification Standards: 

CCV Retention Time Result (ppm& % Rec" 

2.5 ppmv 6.84 2.89 106.3 

2.5 ppmvdp 6.85 2.79 102.5 

'M ust be +/- 10 % of Theoretical Concentration 

Analyst (Intitial & dale): Zl3 \ I \0113 Lab Director (Initial & date): ~7 

tW ~ 

Analyst: 

Response Area 

(mean) 

6536 

14388 

27611 

64019 

162697 

281684 

Calb. Type 

R2 value: 

Intercept (B) 

Lin Const (M) 

ZG 

Calculated 

Concentration 

(From Mean) 

0.12 

0.27 

0.52 

1.19 

3.04 

5.26 

Linear 

0.9925 

0.00 

53584.69 

Recovery 

(+1-15 %) 

112 

99 

95 

110 

112 

97 

Y:::MX+8 

Must be> 0.990 

Included 

00 

f'") 

'" 

~ Po. 
4

.E+05 

3.E+05 

3.E+05 

2.E+05 

~ < 

2.E+05 

1.E+05 

5.E+0 O.E+O 

TNMNEOC (as Propane) Plot 

V 

,1 / 0.00 

1.00 

* ....... ~ 

/ 

2.00 3.00 

Concentration (ppmv) 

/' 4

.00 

y = 53584.691 1 X R2 = 0.9925 

./ V· 5.00 

6.00 

0-

M 

'" 

~ P-. 
Date: 0111012013 Analyst: ZG 

Analvte: Cone. MOL #1 

NMOC 0.050 0.058 

Analvte: Mean Std Dev 

NMOC 0.051 0.005 

FlO MOL Study per SCAQMO 25.1/25.3 

Instrument: GCIFID #4 Units: ppmV 

MOL#2 MOL #3 r.rot #4 MOL#5 MOL #6 MOL#7 

0.050 0.054 0.043 0.051 0.056 0.047 

MOL - Method Detection Limit Study per USEPA Guidelines 

MOL MRL 

0,016 0.0·19 MOL (Method Detection Limit) (7 replicates) = Standard Deviation x 3.143 

MRL (Minimulll Reporting Limit) '"' MOL x 3.0 

Is the spiked concentration <: 10 times the calculated MDL0 N 

Definition: MDL- The minimum concentration of a s ubstance that can be Identified, meas ured <I nd repon ed witl! a 99% confidence interval, that 

the ana/yte concentration ;s greater than zero and is detennined from the analysis of a sample in a given matrix containing the ana/yte. 

Definition: MRL ~ The smallest meas fJ.red concentration of a substan ce (hat can be reliably measured by using a given analytical method. 

o 

"<t 

OJ 

~ p.. 
Alternative Supporting Calculations 

LOD (Limit of Detection) - S~'n arcl Of li., ion x J.O 

LOa (Limit of Quantitation)= St;}IUiiUd Or ",i"ltiQn X 10.0 

f;J] ean Djl Ree • (Mean Res! True ~lua} y. 1001";;" 

Is the Mean % Ree between 80% and 120% ?<£) I N 

r::on c .JMDL ~ Concentml lon I MOL t8\ 

Is the Conc.lMDL between 2 to 5?C!.J1 N 

Siqnal to Noise Ratio· (MeanIStdDev) 

Is the signal to Noise Ratio between 2.5 and 10"G1 N 

Definition: LOD - T/Je lowest concentration that can be determined to be statisticafly different from a blank. 

Definition: LOO ~ The concentration above which quantitative res uffs call be obtain ed with a spec jf(c degree of confidence. 

An.ly!e: POL t= RL rl 

NMOC 0.104 0.104 

Proposed PQL and RL 

Prtlctical Ouantitiltion Limit 

Is the PQL 2 to 5 times higher than the LOQ?(Y}f N 

Reporting Limit 

Is the RL equal to or greater than the POL (5), N 

PQl (Practical Quantitation Limit) = Established by the laboratory based on the abo\le calculations 

RL (Reporting Limit):= Established by the laboratory based on the POL and/or method. 

Definition: POL · The lowest level that can be reliably achieved within specified limits of precision and accuracy during routine laboratory 

operating conditions. In addition, if quatitating a t this level, the lowes t point of the calibration curve must be set at this point. 

Comments: 

An. lys! (sign & d.te): 53 ' \ \ 0 \ 15 L.b Direclar (sign & date): I1!lP" 47J 

-" 

"'" .., 

bIl 

Po< '" 
Appendix C.G PM by SCAQMD Method 5.1 

R0410673 C-10 
SCAQMD METHOD 5.1 PARTICULATE TEST DATA SUMMARY 

ClientiLocatlon. 

Unit 

Sample Location 

Test No. 

Test Method 

Dale 

Start Time 

StopT!lne 

Sample Train 

Pitot Factor 

Meter cal Faclor 

Stack Area (sq h) 

Sample Time (Min) 

Bar Press (in Hg) 

Nozzle Diam (in) 

Stack Press (iwg) 

Slack Temp W) 

Vel Head (iwg) 

Stack. 02 (%) 

Stack C02 (%) 

Met8f Vol (ad) 

MetE)(Temp (F) 

MelE)( Press (iwg) 

Liquid Vol (mI) 

Sid Sample Vol (SCF) 

Moisture Fraction 

Stack Gas Mol WI 

Stack Gas Velocity (Nsec) 

Stack F/aoN Rate (wacfm) 

Slack FloW Rate (dsctm) 

(soklnetrc Ratio (%) 

Facility Average Gas Flow (hsc1h) .. 

FaciWty Average Gas Flow (MMscfh) .. 

Total Weight Gain. mg .. 

Particulate EmIssions 

Grain loading, gr/dsd ..•.. 

Grain Loading C 3% 02 .•... 

Grain Loading 1m 15% 02. 

Grain Loading@ 12% C02 .. . 

Mass Emlss)ons, Ib/hr1 ..................... .. 

Emission Rate. IblMMSCF 

1) '1 IbIhr per Rule 475 PM Limit 

2) 5.71 IblMMsdis stated In the permit as an emission factor 

Gemm. 

Sen~nel 

, 5-2ISTK-PM·50-1 

SCAOM05.1 

21'/20'3 

'4:'4 

18:25 

'9-WCS 

0.84 

0.985 

143.14 

240 

29.35 

0.234 

'.90 

784.8 

1.0467 

14.29 

3.80 

157.850 

76.1 

1.16 

258.1 

148.438 

0.075 

28.34 

89.52 

768.849 

292.783 

101.21 

° r_ 

0.537 

" 

0.0002 

0.0005 

0.0001 

0.0005 

0.42 

0.78 

Reference Temp (F). 60 

Fuel Nat Gas 

Dal a By SP 

'90 

784.8 

1.0467 

14.3 

3.8 

157.85 

7. , 1.16 

258.7 

148.438 

0.075 

28.34 

89.52 

768.849 

292.783 

101.21 

5372.5 

0.537 

, .• 

0.0002 

0.0005 

0.0001 

0.0005 

0.42 

0.78 

Limits 

0.01 

0.' 

5" .71 

Scnwlel U'"I 1 ~O% PM 

Summary 

211912013 

11:33 AM 
14:24 1.3 1.10 1.43 779 1.14 10 78 ! 1:'82.510 7.34 

14:34 1.0 1.10 1.10 780 1 10 79 989.085 6.575 

14:44: 1.1 1.10 1.21 779 : 1.049 10 80 

14:54: 1.1 1.10 1.21 780 1.049 10 ao 

15:29 15:39 10 79 6.74 

15:39; 15:49 10 79 75 6.79 

15:49 15:59 10 80 75 6.52 

15:59 16:09 10 79 75 6.34 

16:33 16:43 S 5 : 0.949 1 10 77 74 

16:43: 16:53 S 1 10 77 74 

16:53 17:03 S 1 I 10 76 74 

17:13 S 0.949 10 77 74 

17:45 ~ 10 . r 77 74 

17:551 10 78 73 

18:.05 10 78 73 

18:15 10 78 73 

Page I 
Del/a~ '"'- -~ ... WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: k"", ~~ LOCATION: -3i# Hk~ I CC;; /1 :L 

DATE: '1 • ) - 1 3 

RUN NO: ;S . ,J. / S - F/YI- 5"<9 - I 

OPERATOR: :6--5 METERBOX 0~:~1~7~k/ k$~---

METER l>.H@: l So Ie 

METER Yd: til . ''15" k 

STACK AREA, FT': J 'I ?,.\ 'i 

TRAVERSE POINTS, MIN/POINT: 5"/1'1 

l>.H= I'J X l>.P: 

Probe Condition, pre/post test: ¢;~ ./ 

Silica Gel Expanded, Y/N:--,-_'7-:,---

Filter Condition after Test: / 

Check Weight: (7 

Meter l>.P 

Point Time Volume, ft' in. H,O 

LJ G t,-\J q 1 C; it E' , Ie"\) l,.,..:) 

S IlIl..'-\ c.. os:. , 1"10 J . :3 

-j \ ,-):'>'i S\ "t.I Sl w i ,0 

:s \"\'\'-\ ''1, "-1.; '1 ') ~j; : . t 

"l. 1'\ Sy '-\ '\ C; .,",, 0 \ \ 

I \ S;;L\ IN,), 1 (.<; I . D 

a \ '> i'-\ {(Jo'f, \ ';fJ 

'" 0 Ie 1(' loor..l. ~(J \ . \ 

S ',~" ! 0 ( ·::; '1 <.::') (, I.. 

"\ , ~V' ( t' n .. i ,\,) , ~ 

~ , -:- 'I' . I'l;), 'i ,'l.. lOt \ • D 

2 t r;)c -. \ I c:>,5 ~ I. ' 

I l \'P l:..cl 1 D'-\' z., ,14() \ , \ c ) ( 1. 1<\ i"'-\'\ ,"", 

Average: 

AMBIENT TEMPERATURE: 

BAROMETRIC PRESSURE-: -'?;-C'~l.7''-,----

- (79' Imp. # Contents Post-Test - Pre-Test = Difference 

ASSUMED MOISTURE:_ ---" iLl1.!.., ""'----,,-:-~~---­ PITOT TUBE COEFF, Cpo 0 ~" 0. \ '1 Fe 

PROBE ID NO/MATERIAL: .. 2-(, (", \ '-, ''';' 1... 

PROBE LENGTH: -I \ > 

NOZZLE ID NO/ MATERIAL: " S ~ NOZZLE DIAMETER: iJ . 'L , cl 

FILTER NOfTYPE: '\"'1",-\"""--:'--,-'1 ,,"'"-?'i':;...::...'--- - - - - - .l:L 

PRE-TEST LEAK RATE:: < ° ,c.'"' CFM@ i 'S in. Hg. 

POST-TEST LEAK RATE: : CFM@in. Hg. 5cr. [Xl L_ PITOT LEAK CHECK - PRE: ~ POST: 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN - '1\""""",- SAMPLER s. <, 

OJ: r 0 q7u 0 ",-tt't,,,,,Q:..J ' ( __ _ 

'/ 171-1 "13(f. y __ 

Mf- 65 r ~-,,-=3.J,-,- , 7-,- __ _ 

6v Of n· () _a-,7:)",-'l ...__ 

SAMPLE CUSTODIAN " l>. Total: ____ __ _ ___ _ ____ _ 

l>.H Stack Probe Filter Imp. Out Meter Temp, OF Vacuum 0 , P. static 

in. H,O Temp, OF Temp, OF Temp, OF Temp, OF In Out in. Hg. % in. H2O 

t c\~ '~ lq i'-' A ,., 1 £\ v I.) 1 '4 i'i 'I '0 \ 0:' (, ~ L ' \ 

\ '-\ ~ '\ 1 "') '""\ , ., f' 1 '-1 '-j'V 

\ . I t> 1'00 4 :;- :-J 1, '-\ ?,:. 

I ,,- I \ lq "ii.c ~Q ~ '"\ 'J 

, \ I .?'.:) 4 <0 ~o '1 " .. '-:L.!'l 

\ 10 I of) 'it '60 " Go r1· a 

\ • "Z \ .g,' " ?lj \' 1S- L\ ;-., 

( , )1.. l ,(,I 41 ~ .. "/ 1 ') '-I , t:> 

\~~ ~L.. 1 03 ,i", - )C-i ,<, ,'. () 

I \ Q ~'-3 ~ . G,"1 ~xJ " .-.... L , 

\ \ 0 '1'(,0 4c, ,,,-\ l 5 y . r ) 

\ . L\ l ()b 4'6 7 1 7 S '-< ' .. U 

~ d ' 

Comments: ____________________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page-l-of 2 

D5834049 

Master Document 5torageiFormsiDatasheetsl Fieid Datasheets 
WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: ~,,,:o .", .,~ p.. 

LOCATION: ~\"'''''llr ... \M_ 

DATE: J\I\') RUN NO: .,.., ) f:.. ii'" - (.>;:,..., . . 'i (~

OPERATOR: q; METERBOX~N7.0~~--------

METER llH@: ,7 

METERYd: /' 

STACK AREA, FT'",: :-;:;r;'i/===--- TRAVERSE POINTS~ NIPOINT: 

llH= __ XllP/ 

Probe Conditi09<'Pre/poslleSI: _ ___ _ 

Silica Gel Expanded, Y/N: _____ _ 

Filler Con~,on after T esl: _____ _ 

Check Welghl' 

Meter llP 

Point Time Volume, ft' in. H,O 

C, v \ ['1 :, I 0'\9. ~"-S- 6,"1U 

? I"~ ., \ D ""-,,,,0 0;) :; c 

4 \,,' ~ IC I.\ , '£,JU \ cG 

~ 1., <;;, \ t') (~ . / i.3LI \ ' 1...' l 

z ~D '> I n'j 'i ('16 t) ,"\0 

J ' \ ~ \ C::;O ~ '.t,~() 010 

[) ' J') -., ! " t:t-.l"W 

i:: c" L\~ \..:: v,k .!.v:'i) \ .() O 

<; \'~'; to '1 3 , (,5D ' . .. ()6 

'1 \ ),,\~' 10.,,, ,;;,cO () ,'jO 

') , lS'S \ '~,S "-J i , '2. 0 

'l., <to'; J 1 ! 2.:c<:k> \ , I 0 

I ~\c.;.. 1.\ \ l. (>, 07_i::> \ J .)0 

(! I u;, ., ~ i:. tp,.." '0 

Average: 

AMBIENT TEMPERATURE: _ ________ 

BAROMETRIC PRESSURE: _____ __ --

ASSUMED MOISTURE: 

PITOTTUBE COEFF, C-p·-. - - ----.-77"-----

PROBE 10 NO/MATERIAL: ./ 

Imp. #Conlents Posl-Tesl- Pre-Tesl = Difference 

PROBE LENGTH: ./ 

NOZZLE 10 NOI MATERIAL:_"'7L7 _____ _ _ _ 

NOZZLE DIAMETER: _ _ "'/..c.7 ____ ____ _ FILTER NOfTYPE: / 

PRE-TEST LEAK R~A"'T"'E"": -: "C;;r<---,C"'F"'M""@;;:---cic-I)...H-;-.,-g-.-

9l P1tf-L- - --

POST,TEST LEAK RATE: :""""',,0 CFM@ <.e~f· 'ii1. Hg. 

PITOT LEAK CHECK, PRE: POST: v 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN '''''''k/''''--- SAMPLER :;""; 

SAMPLE CUSTODIAN ","Ii' 

~L fl \ Tolal' 

llH Stack Probe Filter Imp. Out Meter Temp, of Vacuum 0 , P. static I 

in. H,O Temp, of Temp, of Temp, of Temp, of In Out in. Hg. % in. H,O 

o .1\,\ I /2;-;- N 1\ '-'Ip- C;'"' ,it:' I'~ -:::? ' f") I> .<;" -t""L. . i 

O~'1 ~-\ S'-\ .1 7+ ~ . .;;) 

\ . I '0 ,'6<:' l '7.7 ,'-I 3 '0 

\ ·10 I' '"-I 5'5" 1 0 " '-I 3 ·C 

Ij ,S"I 'l'iY-i ~(.o 'I I 1. '-< ':; 0 

() '<'1 ... . 1'1'::- ->' I '1'/ '1 ~ .\ c, 

\ I D ~\ .:0'(, I I 1':t YO , . , 0 "7 '~? >v, v '1 ' 1 "-\ 3· ., 6 .. r;v-( " 'Ili> \<>0 7/1 7 'J 3('J 

I 'Y' " I fp Ci 1 'I') , ' :3 . r::> 

\ ,-\ 1 r"c;- \"() I () I ~ ~ :'\ 

l ,\ 0 1"'" \ (P't '6 \ I" ?;,.-;, 

'" , 

Comments: _____________________________________________________________________________________________________________ _ 

Date of last revision 1/25/2013 Page t of~ DS834049 Master Document Storage\Forms\Datasheets\Field Datasheets 
DlJlla~ 

PARTICULATE 

SCAQMD 5.1, WET IMPINGEMENT 

Project # 

ClienULocation G"""kN\ eo. 

Sample Location Un; to L Water Blank mg/ml O. C>C>0"G 

Test # 5 Z Itst.!(· P/It·;.·1 MeC!, Blank mg/ml 0,000 

Sample Date 

Analysis Date 

Analyst Initials • 

Item Number 

1, Glass Fiber Filter 55- (Backup Filter) 

I1I(d 

2, Insoluble Solids Filter ~-

J 'i?c> 2. 

3. Impingers and Probe 

Catches 

IlH3-

a. Water Fraction 

b. Organic Extraction 

125 ml MeCI2 ill,C-l 

(5 x 25 ml) 

,;,Dellall 0-.......... , __ 

Date of last revision 11/13/08 

Final Tare Gain Aliquot Net Gain Blank based 

Weight Weight Weight Correction (mg/Sample) on Total 

(g) (g) (mg) (ml/ml) Volume (mg) 

C?l 02.2.. 0·((,2'{ D·O 0 , 0 ---------------- --------------._-

0.1020 0·(1;,23 D·O (:>·0 

--------------- ---------------

nl(.n- 2'·112\ I~ Ek-

('7- S' ).~ 03 

or ~~.c.'m ~"'t:~19- (;>'0 ,:....;.-:: O·c) ~1~ 0·0 

Total Particulate = __ -,-1_. _G, ___ ----'m.:.;.9..... 

Method of Sample Prep/Notes 

DS834012 

Master Document StoragelFormslDatasheetslLab Forms 
......... 

JJella -..- ...... ~ -

SCAQMD METHOD 5.1 PARTICULATE TEST DATA SUMMARY 

ClientILocation. 

Unit 

Sample Location 

Test No. 

Tes! Method 

"''' StartTIme 

Stop Time 

Sample Train 

Pitot Factor 

Meter Cal Faclor 

Stack Area (SQ ft) 

Sample Time (Min) 

Bar Press (in Hg) 

Nozzle Diam (in) 

Stack Press (iwg) 

Stack Temp (F) 

Vel Head fiwgl 

Stack 02 (%) 

Slaclol C02 (%) 

Meter Vet. (&cf) 

Meter Temp (F) 

Meter Press (rwg) 

uguid Vol (mI) 

Sid Sample Vol (SCF) 

Moisture Fracllon 

Stack Gas Mol Wt 

Slack Gas Velocily (ftfsec) 

Stack Flow Rate (wactm) 

Stack Flow Rate (dsctm) 

IsokJnetic Ratio 1"41 

Facility Average Gas FloW (hscfh) .. 

FadlFty Average Gas Flow (MMsdh) .. 

Total Weight Gain, rn9 .. 

Partlcul.te Emissions 

Grain Loading, grldscf ... 

Grain loading eJl3% 02 ..... 

Grain loading @ 15~~ 02 .. 

Grain Loading@ 12% C02 ... 

Mass Emissions, Iblhr' .... 

Emission Rate. IblMMSCF 

1) 11 Iblhr per Rule 475 PM limit 

2) 5.711b1MMscl is stated in the pennit as an emission factor 

Gemm. 

Sentinel , S-2ISTK·PM-75-1 

SCAQ"'D5.1 

21112013 

8-11 

13:22 

19-WCS 

084 

0.985 

143.14 

240 

29.69 

0.234 

1.60 

795.7 

1.2407 

13.35 

.$,26 

168.725 

75.4 

1.38 

384.3 

lSO.708 

0.090 

28.21 

97.58 

838,060 

314,715 

101.94 

0.692 

. , 

0.0002 

0.0004 

0.0001 

0.0005 

0.49 

0.71 

Reference Temp (F). 60 

Fuel Ndt GUl 

Oat. By 

Average 

I .BO 

795.7 

1.24 

13.35 

4.26 

168.725 

75.4 

1.38 

384.3 

160.706 

0.090 

28.21 

97.58 

838060 

314715 

101.94 

6922.9 

0.692 

1.90 

0.0002 

0.0004 

0.0001 

0.0005 

0.49 

0.71 

SP limits 

Limits 

0.01 

0.1 

11 

5.71 

~mind Un;1 2 7~% PM 

SwTII ~ 

2119.::01) 

II:JSAM 
S-2JSTK-PM·75-1 101 .94 : dP Factor ,dH 'n dP".5 TIme/Point In 0", Start End ." Start End Port Point End Start Diff. 

8:11 8:21 S 6 , 15 l .tO 1.65 79ll 1.225 10 64 63 : 794.435 802 .080 1.645 954.9 721 .0 233.9 

8:21 8:31 S i 5 1.6 1.10 1.76 764 1.265 10 70 65 802.08 8099:;(1 7.85 658.6 654.8 203.6 

8:31 8:41 ; S 4 1.5 1.10 i 1.65 793 : 1.225 10 73 " 809.93 817.650 7.72 639.5 637.6 1.9 

8:41 8:51 ~ S 3 , 1.1 1.10 , 1.87 BOO 1.304 10 I 75 70 817 .65 826.000 8.35 997.8 953.1 44.7 

8:51 9:01 S 2 1.7 1.10 1.87 BOO '304 '0 /4 69 B26 833 810 7.81 100 -100.0 

9:01 9:1f S 1 '.5 1.10 1.65 B02 : 1.225 10 73 69 833.81 841.525 , 7.715 384.3 

9:13 9:23 ; E 6 1.0 1.10 , 1.10 789 1 '0 71 6B 841.525 847.800 6.275 

9:23 9:33 E 5 j 1.2 1.10 1.32 i 789 : 1.095 : '0 

, 71 , 6B 847.8 834.770 -13.03 

9 : :33 9:43 E , 4 1.3 1.10 1.43 795 j 1.) 4 10 72 " 834.77 861.865 : 21 .095 , 9:43 9:53" E .! 3 1 2 1.10 : 1.32 799 , 1.095 , '0 i 74 70 861 .865 ; 868.290 6.425 

9:53 10:03 E 2 ! ' .2 1.10 1.32 BO, 1.095 : '0 76 71 868.29 874.660 6.37 

10:03 10:13 E 1 1.0 1.10 1.10 BOO 1 10 BO 74 ; 874.66 881 .680 7.02 ; 

10:18 10:28! N 6 '0 1.10 1.10 795 , 10 83 71 881 .68 ! 888.415 ! 6.735 , , : : 10:28 10:38 N 5 i 1.0 1.10 1.10 796 , 10 ; 84 79 888.415 894.370 5.955 

10:38; 10:48 N 4 1.0 1.10 1.10 795 , 10 i 84 BO 894.37 900.320 5.95 , i , 

10:48 10:58: N , 3 '.2 1.10 i 1.32 796 ; 1.095 10 B4 SO 900.32 i 907.710 ; 7.39 I i 11:08: 

, ! , 10:58 N 2 1.2 1.10 1.32 796 : 1.095 10 83 80 907.7 1 914.e55 ; 7.145 

11 :06 11 :18 N 1 , 1.2 1.10 1.32 796 1.095 ' '0 64 BO 914.855 : 922.000 1.145 

12:22 12:321 W 6 U 1.10 

! 

1.21 764 1.049 ' 0 BO 79 . 922.000 928.052 6.852 , I 12:32 12:42 W , 5 ' .0 1.10 1.10 798 I 1 10 i B1 79 : 928.852 ! 935.000 i 6.148 : 12:42 : 

, _. 12:52 W 4 i U 1.10 1.21 796 ' 1.049 i '0 I BO 78 935 ! 941.600 6.6 I . , I , 12:52 13:02 W 3 1.3 1.10 1.43 799 . 1.14 ! '0 80 78 941 .6 948.805 7.205 

13:02 : . I I : 948.805 ; 056.010 i I 13:12 W I 2 '3 I 1.10 1.43 798 1.14 10 I BO 78 7.205 I , , 13:12 13:22 W 1 1.2 1.10 1.32 795 i 1.095 10 BO 1B 956.01 963.16 7.15 I 

\ ·Avg. 1.24 1.375; 795.7 1.1141 240 75.3958 168.725 i I , I 

Page 1 
WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: tv~ ",,,-

LOCATION: 3::'; ~t;" ~.) f,{ ..... =T 1-

DATE: J. -I ~ r;3 

RUN NO: :5 - ;)-/ Sn<' P/YI - 7';-- I 

OPERATOR: :55 METERBOX7N ~: ~17~kJ ~----------

METER H@: \&' ce 

METER Yd: t . ..9: "H 

STACK AREA, FT': l '"q ·1 'l 

TRAVERSE POINTS, MINIPOINT: 5/~'1 

~H= X~P: / 

Probe Condition, prelpost test: ~/ , 

Silica Gel Expanded, YIN: _ 

Filter Condition after T est:------'-, "'/7------

Check Weight: --V 

- - -- . _ -- -

Meter P 

Point Time Volume , ft3 in. H2O 

S [) 1il'6\\ ,""C\;, '"\',,>$ \,E:C 

S; 0 "::l2. , '00 1 ,060 \ , L"u 

't 0"'3 1 ~.:)q .,30 , S0 

3- c'!>'\1 'CI1,(A5o \, "].:' 

2- o bSI Q,~ .00L> \ '1';-

I 0"'01 '(,'3 -;, , .,,'" \. '::>() 

o c'll " -II . S< :.. I~ t; Q~ \ .)) J~,"\ . ;. / !.., I I I'lD ",., J."\ t,.L -\ 1 ""'JCv \ . 2/:: 

L ')~I ; 1 ~;"'1" '. \lu , ~I..) 

Ul l'1. '1 :'/ ~ ,. '3.;1) 1 ~v 

;) '1 .:., ',:' i{ 'r, :I '''',!''''' I . -'

-~ -

i 2"i'c£'/ C';, '\ iAn..' \. ', e") 

0 lCI~) y,,-i", \ ,l,,\COO 

AveraQe: 

AMBIENT TEMPERA TURE: _ ___ 1L <eJ"' ·--o ____________ __ 

BAROMETRIC PRESSURE: 

ASSUMED MOISTURE:,-cc:-_if";;+,i.'\:= ______________ _ 

PITOT TUBE COEFF, CP:-:--.'if2'-':;->'7!N-:-;"'-:75"?""--r-c=-;:T 

PROBE 10 NOIMATERIAL: if --z...(" '>'':1 p;s- I j\"~.s PROBE LENGTH: l' , I 

NOZZLE 10 NOI MATERIAL :."'7"'1~7t7.!..;::.\\_"" $'------------- NOZZLE DIAMETER: 0 , 21 ~ I 

FILTER NOfTYPE: '--;"I"'1UC;:"C2;-:r1 ~S""5 &------------------

Imp. # Contents Post-Test - Pre-Test = Difference 

J.. 

.8 

L-/ 

qc,oi-j 7=.1 !,O~ __ 

___ !is t , G -",""" ,(t(~=g _ _ 

Cl~ ).JHi 

II 

Mi- ?JC!.)~ b37, If; 

{)~ CfC(? J' 9' 53 , I 

-- PRE-TEST LEAK RATE: : <'DoOD$" CFM@ I C; in. Hg. LIla "' I 

POST-TEST LEAK RATE: : CFM@ in. Hg. /"-' f ) _ ~(2\ ilh' -,00 

PITOT LEAK CHECK - PRE: V-- POST: 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN -.,.--A---- SAMPLER ~ 

SAMPLE CUSTODIAN ~ Total: ___ _ ______ _ ___ _ _ 

H Stack Probe Filter Imp. Out Meter Temp, OF Vacuum 0 2 P. static 

in. H2O Temp, OF Temp, OF Temp, OF Temp, OF In Out in. Hg. % in. H2O 

1.10", 1 5'0 ,.,.-q .. f--.l[A C>l ~ (,~ '-/--. t\ I' <;z., .... J. - I 

I .-Y ... " I '0'\ I";; , '")0 t" '> " ' 0 

\\.-(" ,,,.,, ~'6 ,3 l,,( '/ .0 

1 5 1 "&0(\ 1..1'0 'l ( 10 l' \ ~' I P:,cc\ '-1-'1 '1,"\ ("9. l -6 

\ ,lD 5 9--0 2.- Sa 1 5 ic,,! 't, O 

I d ') I q.,ri' . • > 'II L 'C. ,-\-.0 

\ J;L 1-:'1 'I" ') 11 ,-,,", L\..O 

~ ·'-\-3 -I f' 'J 49 7;;1. (,,'1 'j-'n 

I " .' . )'" '\ :"'0 ")'"1 ' /0 if ', '1 

\ .-~ , ' Qj\ ::--'"'"' -, If' -I I 'r i) 

...1 cl. n 7W;:i ~~ .- ':'~1 . I '-t' <j. () 

" !---

._-

Comments: ____________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 page l-of 2-

D5834049 

Master Document StoragelFormslDatasheetslField Datasheets 
Della!1 

... --.- WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: ~c. ,,,, ,,,1'1-

LOCATION: <;:C ""'''' !).LDATE: .1!..\'1 \ \ 1 

RUN NO: So -c.( s";\- - f,V' -~ 1 

OPERA TOR -;-;; -,::..2:,::;---:c:-;-c ___ _ 

METER BOX NO: '. --:.0~ 2' 

METER dH@: _ _ ___ -r _ _ _ 

METER Yd: STACKARE~A~,~F=TT:----,L--------

TRAVERSE POINTS, MI OINT: __ _ 

dH= _ _ X dP: 

Probe Condition, p post test _ ______ _ 

Silica Gel Expa ed, YIN: 

Filter Condition after T est-----------

Check Weight _________ __ 

Meter dP 

Point Time Volume , It' in. H,O 

1,1 (, Ie 1'1< 'Q"i ,(8::- i , -) 

'> , 21<' Wi:Sa· '11 ~ I, () 

'I t ,,;. "\ ~ "::s. '-t . 0,7 1 \ . () 

? . "'q~ 0; c~ :]LL \ . /-

'1 . ';)<;'l? Cl'" :11 [l 1,3L 

I \ \ Co~ ,G) l '-\ ~55- 11..-

\I.) P i \ I.;l, ''\ '). )..., DN' 

(, 1\ L. L. "\). ~ . c"i) 1. 1 

( II l. r:l Lr-,? . r3t

5:L I . i) 

' I \, .... \ 2. ':)7,5 ' CtO i ' I -') IIS "'-- '1 '\ I · !,CO I , ) , 

1- 1'7 .... L'L. "L\'(" '{,c5 1 ~ 

- ) 

"'1. \ (.. ,,\S(,.· ,OIO , -Z 

() ) '- Z- 'Z- O(,!-. I ("O 

AveraQe: 

AMBIENT TEMPERATURE: ,/ 

BAROMETRIC PRESSURE: ;> 

ASSUMED MOISTURE: c 

PITOT TUBE COEFF, Cp:__ ;> 

PROBE ID NO/MATERIAL: ______ --,,..<c'--__________ _ 

PROBE LENGTH: /? 

NOZZLE ID NOI MATERIAL: 7 

NOZZLE DIAMETER: __ ---,7c-________________ _ 

FILTER NO/TYPE: / 

PRE-TEST LEAK R"'A"'T"'E'--: ~: "--------;C"'F"'M-;:@;:-------oi-n.-,H.,-9-.-

POST-TEST LEAK RATE: : CFM@ in. Hg. 

PITOT LEAK CHECK - PRE: POST: 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN --/k-~--

, .. rc l- c i SAMPLER 0; 

:;'<: '" >-') SAMPLE CUSTODIAN .'r' 

dH Stack Probe Filter Imp. Out 

in. H,O Temp, OF Temp, OF Tern , OF Temp, OF 

I . I . It? ~ N IO>- ,J' ~~ 

i , i /'1 10 ~ 

i \ 1"'1 ') ,-' <- ~~ " c\f.r S '1 

\ .:; J,ll I l ie ;;-, 

1-l!:L 71b 7 

\ , 2-4) 1 '~-I (. I 

\ i I tl ' Iei '':;' Co , 

I ?-f' u"5 ;:. 

I '-I '') '),'I c/ Cd 

I '-\ :> 'I '\ 'l!! ( -" 

\ . -:; '""L 1\ '" b ~.?,. 

, 

Imp. # Contents Post-Test - Pre-Test = Difference 

/ 

L-

~ .. ; /'// 

---- --;:r'---------

/,/ 

---7/ ·- - -------

//' / ' 

/ 

.' 

Total: ____ _ ______ __ 

Meter Temp, OF Vacuum 0 , P. static 

In Out in. Hg. % in. H,O 

-.;.;:. ~, \ '"\ ,7 ... ! 1.:; I - Z 1 

'i.~ 'i lct 4' .) \ 

'0 '-\ "::':-0 '1' J 'i <i.'l(.l y .U 

,(I') \"'Ll '4 -0 

){4 '}(O 'I. b 

i"y..) 1 -- ~/ 

'3 \ I"!. .~ 7-. 0 0 '1. ~ _<f -Ito l 't 4-, () 

-?IO '1'"6 '--i u 

'at....' '1 'd ... \ -c.) 

-J----

Comments: ____________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page ',J of ), -- - -

05834049 

Master Document 5toragelFormslOatasheetslFieid Oatasheets 
Del/ab. -"'--,- WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: L-tl.M'-"-

LOCATION: ,-;< _",t.' . - r It, -," ? 

DATE: {c:..0) ~~ RUN NO .. 5 -Is - fA'l - 75 -I 

OPERATOR: b METERBOX~N~0~:~~171Z~~~·~~·----------

METER AH@: \''''iP 

METER Yd: O· if 1 ~ 

STACK AREA, FT': 1'1:, ·,,-/ 

TRAVERSE POINTS, MIN/POINT: 

AH= ..-l...!.L X AP: 

5/')->1 

Probe Condition, pre/post test _____ _ 

Silica Gel Expanded, Y/N: ______ __ 

Filter Condition after Test ______ __ 

Check Weight __________________ __ 

AMBIENT TEMPERATURE: "] ~" BAROMETRIC PRESSURE:~jj:=I-'\i.;-' r" -------

ASSUMED MOISTURE:".,-"''t...:,CJSC.-.;;:,.-_ _ _____ _ 

PITOT TUBE COEFF, cp:.-,---\riJ~,,:::~'7"- =- _,_7.7'c:_:_ 

PROBE ID NO/MATERIAL: t/?-" 6 ';'t""- 11/ ... ,6 

PROBE LENGTH: ' ./ ' 

NOZZLE ID NOr MATERIAL: - .s. "'I-r...... 0'·)3'1 

NOZZLE DIAMETER;,, : --"1O:....T;).:,:3"'Vf~ ________ _ 

FILTER NOITYPE: ., 

PRE-TEST LEAK "'A"'T!::E~: "': .....!", ,"'·<G5"'= -?-cC"'F=M7@=-·' ..... "'----cic-n.-cH7g-.-

POST-TEST LEAK RAT .: v9'M@ in. Hg. 

PITOT LEAK CHECK - RE: POST: 

CHAIN OF CUSTO SAMPLE CUSTODIAN .----- / 

SAMPLER .;", 7 

SAMPLE CUSTODIAN,_7"''-

Point Time 

Meter 

Volume, ft3 . AP . AH / 

In . H20 ,n . H20 , 

Stack 

Temp, OF 

Probe 

Temp, OF 

Filtey' 

Te.w. OF 

Imp. Out 

Temp, OF 

Lcl Co 

5 

...j 

:> 

2. 

I 

IS.. Et.I 0 

~ 

7 

--'t 

\ '" ,1 I \ '-1;1..:1 

dJ'1 

1'\ '+1 

\ '-IS? 

'''01 

IS (1 

1"'20 

\S3v 

'-14, ,'3\0 \ .. ,)0 i ( "to 1<j~1; 

'1"-\1 . <&1{) \. sv I/f.C\~ ., t; 

1","" o'l5i, \ . :;iil V \ ,"1.3 .. '19 

\ b 1. . :l,lO \ ,!'l]l/l 1.32. catv 

"1(,,,\ ,OOC) \ ,;t<') I 1 , 5'2..... Bel 

II S',("aJ y.'l..D I \ ·32. '60'1 

'Vb.L;tOO L 

"\ II '--< 50 / L I Il...l I ",,\'l ..., .. q ;-;'10. 

7. "'-ro(:' \,,~T - PI"-{>~ L 

'-I ,. 1 t~~ / / 3"' \~ / / "- 'T' I \~ / L \.~~ / / 

END 1/ / 

/ / / Aver,,~_ L ~ L 

Comment /1(4- IIDlde c6 t.- 1i \ / 

/ 

/ 

£1:0. dJA ~::;q 

/ So 

~r 

L "=':2. 

s.:3 

/ 'iU 

L 

/ COl 

v 

Imp, # Contents Post-Test - Pre-Test = Difference 

.;>;: ~r~1 7.3~3 --"..C'-=-___ _ 

" (; will __ _ 

:5 /0 t-

:!......Ab-

__ bJ6'D __ 

__ 1Jl.t.. 

J;. " .k "- ,/2,' I.·>,t' - i () 0 

Total: _ _ _________ ___ _ 

Meter Temp, OF 

In lOut ,?-.. i ld-... 

''i T l.1 

L'i 1'1.'2.. 

I ,e; 1'1 \ ,.,. I -rl 

1(.. I~'l,:l.. 

'1~ 1 1.), 

Vacuum 

in. Hg. 

3D 

'3; ." 

'3D 

:3, -) 

'<. ..... , 

3 ' ("'1 

~/ ) 

02 p, static 

% in. H20 

\;)c>' I "'Z.O 

'" 

Date of last revision 1/25/2013 Page .2-.. of '2 

DS834049 

Master Document StoragelFormslDatasheetslField Datasheets 
8011a/1 

PARTICULATE 

SCAQMD 5.1, WET IMPINGEMENT 

Project # 

Client/Location GJl.t'\.:M"'- ;'/1/).0(.3 

Sample Location Un; t. Z Water Blank mg/ml 6.000« 

0 . 0000 

Sample Date 

Analysis Date 

Test # 5Z./~iK· PM·.S·I MeCI2 Blank mg/ml Analyst Initials 

• 

Item Number 

1. Glass Fiber Filter f;£,,-

(Backup Filter) 11-~1 Z. 

2. Insoluble Solids Filter l+ 

55"~ 

17'<'7 

3. Impingers and Probe 

Catches 1l2.'£" 

a. Water Fraction 

b. Organic Extraction 

125 ml MeCI2 t(HI..( 

(5 x 25 ml) 

Date of last revision 11/13/08 

Final Tare Gain Aliquot Net Gain Blank based 

Weight Weight Weight Correction (mg/Sample) on Total 

(g) (g) (mg) (ml/ml) Volume (mg) 

0.\")1.-\ a·lnS- D.() 6 . 0 -------------- -----------------

0·\ hi '3 D.lfA:; 0 ·0 ---------------- 0·0 --------------

(. -g 

2Y. 2'iH3 1.9 ::..--- ~'i.2>r- 2. I. "I 63 ~-::r5 

2. .... tO~!> 7. f: '1-f'l'f D·O ~ ~15' o.c) 00 

Total Particulate = __ I_·_'1'---___ -'m.:.:.9;;z... 

Method of Sample Prep/Notes 

DS834012 

Master Document StoragelFormslDatasheetslLab Forms 
SCAQMD MeTHOD 5.1 PARTICULATE TeST DATA SUMMARY 

CHent/Location. 

Unit 

sample Location 

Test No. 

Test Method 

Date 

Start TIme 

Stop Time 

Sample Train 

Pitot Factor 

Meier Cal Faclor 

Stacl< Area (sq ttl 

Sample Time (Min) 

Bar Press (in Hgl 

Nozzle Diam (in) 

Stack Press (iWgl 

Stack Temp (F) 

Vel Head (iwg) 

Stecl<02 (%) 

Stack C02 (%) 

Meter Vol (aef) 

Meter Temp (F) 

Meter Press (iwg) 

Liquid Vol (mil 

Std Sample Vol (SCF) 

Moisture Fraction 

Steck Gas Mol WI 

Stack Gas Velocity (ft/sec) 

Stack Flow Rate (wacfm) 

Stack Flow Rate (dscfm) 

Isol<lnellc Rallo (% ) 

Facility Average Gas Flow (hsclh). 

FacHity Average Gas Flow (MMscfh) .. 

Total weight Gain. mg .. 

PartIculate EmissIons 

Grain Loading. grldscf .. . 

Grain Loading@3%02 ..... . 

Grain Loading@ 15% 02 .. 

Grain Loading @ 12'1" C02 ... 

Mass Emissions, Iblhr' ..•... 

Emisskln Rata. IblMMSCF 

1) 11 Iblhr par Ruts 475 PM Limit 

2) 5.71 IblMMsef is slated in the permil as an emission factor 

Gemma 

Sentinel 

2 

S-2ISTK-PM-l00-l 

SCAO~:J5 1 

113012013 

9:26 

13:34 

H -WCS 

0.84 

0.996 

143.14 

240 

29.80 

0.234 

2.00 

760.6 

1,6957 

13.0/ 

4.42 

194,245 

70.7 

1.89 

466.9 

189.687 

0.1 03 

28.08 

113.4 1 

974.034 

366.608 

103.29 

~ .. 1' 0.846 

, . 

0.0003 

0.0007 

0.0002 

0.0009 

1.02 

1.21 

S-2ISTK-PM-l00-2 

SCAQMD5.1 

1130/2013 

13:45 

17:51 

H-WCS 

0.84 

0.996 

143.14 

240 

29,80 

0.234 

2.00 

781 .9 

1.5498 

13.24 

4.34 

184.450 

67.0 

1.77 

415.3 

181,305 

0096 

28.14 

108.35 

930.578 

352,398 

102.71 •. 

0.824 "

0.0002 

0.0004 

0.0001 

0.0005 

0.54 

0.66 

S-21STK-PM-l00-3 

SCAOMD 5.1 

113112013 

8:33 

12:39 

H -WCS 

0.84 

0.996 

143.14 

240 

29.68 

0.234 

2.00 

779,0 

1.7181 

13 ,o..~ 

4.42 

196.210 

78.5 

1.94 

462.5 

188.068 

0.103 

28.08 

114.31 

981 ,755 

368.538 

101.88 

0,826 

2.6 

0.0002 

0.0005 

0.0002 

0.0006 

0.67 

0.82 

Reference Temp (Fl. 60 

Fuel 11..11. Gas 

Data By SP 

Average LImits 

0.84 

0.996 

143.14 

240 

29.76 

0.234 

2 

780,5 

1.6546 

13,13 

4.39 

191.635 

72.1 

1,87 

448 

186.354 

0.100 

28.10 

11 2.03 

962122 

362515 

102.63 

8319.3 

0.832 

2.9 

0,0002 

0,0005 

0,0002 

0.0007 

0.75 

0.89 

Limits 

om 

0. 1 

11 

5.71 

Scnll ncl Un;1 2 JI Nl% PM 

Sunu"ary 

2/ 19/2U13 

1137 AM 
S 5 2.5 1.10 2.75 775 1.581 10 67 63 175.430 9.58 

S 4 2.5 1.10 2.75 776 ' 1.581 10 68 65 185.040 9.6 1 .. S 3 2.5 1.10 2.75 781 : 1.581 10 6' 65 185.04 194.650 9.61 

S 2 2.0 1.10 2.20 " 0 ' 1.414 i 10 70 66 194.65 2U3.900 9.25 

S 1 1 

10:37 10:47 ; E 5 1.6 1.10 1.16 780 1.265 10 7. . 9 7.9 

10:47 10:571 E • 1.3 1.10 1.43 781 1.14 10 7. 6' 75 

10:57 11:07 : E 3 1.8 1.10 1.98 73 69 7.9 

11 :07 E 2 1.5 1.10 1.65 72 69 7.675 

W 5 1.5 1.10 1.65 1.225 75 71 267 273.800 ' 6.8 

1.2 1.10 1.32 1.095 75 72 273.8 281 .720 7.92 

1.5 1.10 1.65 10 76 73 281 .72 289.440 7.72 

1.8 1.10 1.98 10 7G 289.44 I 297.640 8.2 

1.7 1.1 0 10 71 72 31 4.14 322.130 i 

1.6 1.10 10 71 71 322.13 329.900 

1.6 1.1 0 10 72 71 329.9 337.710 7.81 

1.0 1.10 10 72 70 337.71 344.285 6.575 

Page 1 
S-2/STK-PM-l00-2 

Start 

13:45 

13:55 

14:05 

14:15 

14:25 ; 

14:35 

14:48 

14:58 

15:08 : 

15:18 ; 

15:28 ' 

15:38 

15:50 

16:00; 

16:10 . 

16:20 · 

16:30· 

16:40 

16:51 

17:01 ] 

17:11 

17:21 

17:31 

17:41 

End I 

13:55 , 

14:05; 

Port 

16:00: 

16:10 

16:20; 

16:30 : 

16:40 i16:50: 

17:01 

17:11 

17:21 ; 

17:31 i 

17:41 : 

17:51 

w 

w 

w 

w 

w 

W 

N 

N 

N 

N 

N 

N 

E 

E 

E 

E 

E 

E 

s 

s 

s 

s 

s 

s 

; 

, 

I .. ; 

I 

Point ·dP ·Factor,dH ,dP'" Time lin 

102.71 

6 

5 

1.50 

1.20 

1.00 ! 

3 _; 1.40 : 

2 1.40 ' 

4 

1 1.00 · 

6 

5 

4 

3 

2 

1 

6 

5 

4 

3 

2 

1 

6 

5 

4 

3 

2 

1 

1.80 

2.50 

2.50 i 

! 2.80 , 2.80 · 

2.50 , 

. 2.30 I 

. 2.50 i 

i 1.00 I 

'," 1. 00 : 1.20 

1.20 

1.30 ' 

1.30 i 

1.20-1 

1.20 · 

1.00 

1.00 

1.55· 

1.10 1.65 793 

1.10 1.32 776 

1.2 

1.1 

10 

10 

10 

10 

: 1.2 10 

1 10 

1.10 : 1.10 : 771 

1.10 1 1.54 : . 760 

1.10 ' 1.54 770 

1.10 1.10 782 

1.10 1.98 i 

1.10 , 2.75 : 

780 ..1-3 : 10 , 

779 1.6 10 

780 1.6 10 : 

780 ; 1.( 10 

782 ; 1.7 , 10 

785 · 1.6 ' 10 

1.10 ! 2.75 

1.10 · 3.08 

1.10 : 3.08 : 

1.10 2.75 · 

1.10 · 2.53 ; 

1.10 ; 2.75 ; 

1.1O i 1.10 : 

1.1.0 ; 1.1.0 . 

1.10 1.32 

1.10 1.32 i 

1.10 : 1.43 i 

1.10 1.1.43.; 

1.10 I 1.32 

1.10 1.32 · 

1.10 1.10 

1.10 . 1.10 : 

: 1.77 

785 1.5 , 10 

786 : 1.6 ; 10 ! 

786 1 1 10 

787 ! 1 10 j 

787 11.1" 10 

780 1.1 10 

785 1.1 : 10 

784 1.1 1 10 

786 1.1 ' 10 ! 

787 1.1 · 10 

787 1 10 

787 1 10 

781.9 1.2 ' 240 . 

Page 1 

69 

70 

70 

70 

69 

69 

69 

70 

70 

69 

69 

69 

69 

69 

69 

68 

68 

68 

68 

69 

69 

6' 

69 

69 

Start Eod 

66 354.550 362.400 

66 ; 362.400 ' 369.1 90 : 

66 ! 369.190 ! 375.790 : 

65 375.790 383.230 

65 383.230 390.530 

64 390.530 397.055 

65 397.055 405.215 

64 405.215 i 414.875 

6.4 · 414.875 · 424.330 

64 ; 424.330 . 434.700 

64 434.700 444 .725 

63 444.725 454.265 

72 454.265 463.500 

72 : 463.500 473.100 

64 l 473.100 ! 479.600 

64 ' 479.600 . 486.100 

64 - 486.100 -. 493.000 ~ 

64 493.000 499.485 : 

64 499.485 506.290 

64 506.290 513.150 

64 513.150 519.935 

65 519.985 5.26.770 

64 526.770 532.710 

64 532.710 539.000 · 

67.042 i 

ft3 

7.85 

6.79 

6.6 

7.44 

7.3 

6.525 

8.16 

9.66 : 

9.455 

10.37 

10.025 

9.54 

9.235 

9.6 

6.5 

6.5 

6.9 

6.485 

6.805 

6.86 

6.835 

6.785 

5.94 

6.29 

184.45 

Eod 

955.2 

878.4 

664.4 

947.9 

Start 

727 

656.5 

640.9 

900.2 

100 

Oiff. 

228.2 

221.9 

23.5 

41.7 

-100.0 

415.3 
8:43 S 5 2.50 66 552.500 562.030 9.53 

8:53 9:03 S 4 2.30 776 10 79 70 562.030 571 330 9.3 

9:03 9:13 S 3 250 10 81 73 571 .330 531.150 9.82 

9:13 9:23 S 2 2.50 i 10 eo 74 581 .150 5<"}0 540 9.39 

9.99 

9:45 9:55 5 i. 9.12 

9:55 10:05 9.145 

10:05 10:15 465 l 10:15 10:25 

10:47 10:57 

10:57 11 :07 N 

11 :07 11:17 N 

11 :17 11 :27 N 

11:49 11:59 W 10 '" " 704.730 

11 :59 12:09 I W 10 60 78 711.920 

12:09 12:19 W 10 B1 78 719.410 726.480 

12:19 W 10 63 7. 726.480 73.030 

Page 1 
1IIJ11af). .. ~---

CLIENT: q E M Nt Pr 

LOCATION: G N . ( r0ftlDATE: 0 I 

RUN NO: ~ ;. ,,\<. - M - . \'.:.'0'- . 

OPERA TOR :=,....;.$".S~--:-c:-:-___ _ 

METER BOX NO: I:.J ""' '- ') 

METER m@:._J.\ ..:,.;;5":1.-'-"G ____ _ 

METER Yd: () 4'1", 

STACK AREA. F'f': l'P , \"1:. 

TRAVERSE POINTS, MIN/POINT:...:I",.:>.!...I __ 

IIH= -41- X t.P: ./ 

Probe Condition, pre/post test:-=,/-.-.:.V __ 

Silica Gel Expended, YIN: ~ 

Filter Condition after Test: 77 

Check Weight: __ ~ . .c.Z _____ _ 

Meter t.P 

Point Time Volume, 1\' in. H,O 

S " d-i.'JJ ... L ,'j.(" J ('l>S' 9..?> 

'- /9"\3\:> \ G ." 'GS() ":{ , .":I 

"1 01"<t 11'5 H'D ..l. -'? 

", 6..::\s;~ I ,?"".~ . <; 

- ( \) .:) t;;> ,c.: "J I.>,;u 1 ·0 

\ (.:l'''' -z.,)':t, 't ~q'U ~.-o 

0 lOLl" ·AIA.. 630 

E C, lVAI ?-.\ ?. -°30 I , L. 

S . 0-'>1 :2-:2 ",,0, c;. < \ . c.." 

'f 110 -\1 ';). ;).. l , "\6 , , ":, 

.;, (0 ,,1 ~,",S.I'\() \ 'i) 

z. 1\ en ~ 'i " , JOI) ~ 5 

I 11 \'1 ,,-.,,, <" 1'1 ") I..'::> 

n 1\11 :JSCI). 1.,tI"'J 

Average: 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET 

AMBIENT TEMPERATURE: 'lfl " 

BAROMETRIC PRESSURE:-: --,,("'O""",'jJ"'er::::------

ASSUMED MOISTURE:.-,-_--'q ..... --"L/L- I ---:-_-----

PITOT TUBE COEFF, Cp: "f~ P<' 

PROBE ID NOIMATE~IAL: it v-.-? \e, 27 

PROBE LENGTH: 1 ' 

NOZZLE ID NO/ M:-:A-=T=ER:'::-I::-A:-L:------::-:2d 

NOZZLE DIAMETER: 0 , 7. ') c) 

FILTER NOITYPE: '::>5 - n ,q) PRE-TEST LEAK RA::-::T=E~: :-: liT-:-', . ...., ub..,.~C-:=F"'M-:::@:--71 -''"5,," ----,i-n.

7H;-g- . 

POST-TEST LEAK RATE: : CFM@ in. Hg. 

PITOT LEAK CHECK - PRE: . v POST:.--,-__ 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN.,...-# 

SAMPLER >? 

SAMPLE CUSTODIAN NF 

t.H Stack Probe Fmer Imp. Out 

in. H,O Temp, OF Temp, OF Te"!I , OF TerTlJ>, OF 

-:J. . '::> '" Tll tvl", 1"1 ,1 sro 

'J. 'l ~ ( I c., ~j " ;<·1 '5" '11 V' ..':t..-2' [,),S ·7b. \ 'i-; 

;;2., . '2..0 1~6 '\ ..:>. 

.R . ?cD '\"',;0 '::li 

\ ·7('" '1 ' (,;. <.\-'-'\ 

\ . ', l.o " b<> "",\ 

i.--\-;' 11 \ ttL{ 

\.'1'(, "1 0., :z Ll'::> 

I ,t r..-., I'" ~ '+<)' 

llP< W ·<., 1.\(,.. 

Imp. # Contents Post-Test - Pre-Test = Difference 

I pr\~o jo<i\,Z. 1",1'5,5 

?. v:t 1-\20 CJ33'i JS\ ~ 

3 N., 1:.2'7, 1 lo3b, '2., 

.:i. S~ ~b b g":;(,j 

\)1:- \\1..0 l_Nt;; i2-(~ -\t>~-D 

Total: ____________ _ 

Meter Temp, OF Vacuum 0, Pstatic 

In Out in. 1::19., % in. H,O 

I ). (".2:. J!:..O (~ iM 

\,\ ~,'3>. (p .O 

{,...f.. ["...2: (, u J. 

l.9u.> loS G, C 

ill. _G,J;,. ~o ..l. 

~() l<>G 0, ~ J. 

/ 

1"- i..'fi ':>0 

"ILl" '-"''''I 5"6 

" \.\ 10'1 ':>'0 

'/:L., io"l S J 

'l;;J, ..h5. SLl 

7.5. 70 ....s..~ 

/ , .. " . 

Comments: (7("~ \ of 'ZDate of last revision 11/13/08 

----

DS834048 

Master Document StoragelForrns\DatasheetslField Datasheets 
JJeIIab.. ~--.-

CLIENT: l?=,f;,," M " 

LOCATION: s", '" '\ '" "''-

DATE: \ 1 "'''1 ("2 RUN NO: S'~ 21 .>",<.· r",- 10" -I 

OPERATOR: ., ~ 

METERBOX~N~O~:~~---- ---

METER "H@: i 

METER Yd: STACKARE=A,~FT~2;---------

TRAVERSE POINTS, MINJP.0INT: __ _ 

"H= X "P: / ' 

Probe Condition, pre~p sf test: 

Silica Gel Expended IN : 

Filter Condition afte Test:============ 

Check Weight: _____ ___ _ 

Meter "p 

Point Time Volume, ft' 

WL. 1\ 2,Z- .,,{ "''6,If>'tS ~O . U .. 

5'i- ' II'\L.-. . ' I, 

'I \ \ Sz- ) l" , 'Ooc.> \, ::2 

.> \ lO1. ~Li .'-=iCC? :> , c; 

2 \ liZ- ;,lit1' '1'10 \. 'il 

\ 11. '1. l ',z", 16"\u 'J. ,[) 

0 I <..~·7_ " ,01:<,\(-4 

N " \ 1. "1 :'0 \:0 .1" ) ;p, 1 

~ , 2 '\'t "'i'L, 'f0 \ ., 

'-\ ,L ' ''1 ." 'L'{ .,:,u I • L. 

" \ ~CLI :z. :2 "\ "1 00 \ ,(,. 

'" \ I'i ') ")'1 .. <I 0 10 

I I 3 ·J·"I ., '-\ '-\ :l. """ L • 

IJ t y'3L{ '>c,"\OO 

Average: --

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET 

AMBIENT TEMPERATURE: / 

BAROMETRIC PRESSURE: 7 

ASSUMED MOISTURE: Z 

PITOT TUBE COEFF, Cp: / 

PROBE ID NOJMATERIAL: ___ ",,-- / ______ _ 

PROBE LENGTH: / 

NOZZLE ID NOI MATERIAL: / 

NOZZLE DIAMETER: __ + _______ _ _ 

FILTER NOITYPE::::-:-:;=-+ __ =~,_--__:__;_;_- PRE-TEST LEAK RATE' . CFM@ in. Hg. 

POST-TEST LEAK R E:: -; 0, "'" CFM@ I'" in. Hg. 

PITOT LEAK CHEC - PRE: POST: v 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN -;A<>,c"--

5~ SAMPLER ----;; 

f' '" ::," \ SAMPLE CUSTODIAN A{>r 

"H Stack Probe Filter Imp. Out 

in. H2O Temo, OF Temo, OF Temo, OF Temo, OF 

I~I, ,."1 N/A t"'A l.\e 

I ,l,? '119 '-11 

\ ,Y2.. '11 "1 '-\'0 

I .L, '-- "PdL LI" 

\'i Yl I~ '') '1'i ~Q ,ca4 ; "t'1 I 

\ I 'U I I'D \ ; S ,) 

\ ,bl 1"')0 "'0 

I. ' ll;> l<61 I.~i 

I I t..> L'0 \ ; S) 

\'\ 1 c:ct; i sl 

( \ 1'65 : 5'''-

I 

\ 

v\ 

y 

- - --- - ---- ------ --

Imp. # Contents Post-Test - Pre-Test = Difference 

7 

/ 

,,/ 

/' 

// 

Total: ____________ _ 

Meter Temp, OF Vacuum 02 Pstatic 

In Out in. HQ. % in. H2O 

7.") l).. ~<' \3" .~~, ' ) , I 

'1 5 ~\ ~() 

I S 1.) .. ")c 

lb 7" S C) 

'lio 7".:. 5 Ll 

lLo 1"1.. A 

1'f 7':> C, ,./J 

,I ,;).., <;. " I 

11 I 1 '5 

l')"" II S-" 

"J':<' 1'-' t;'(, 

1)... 70 S 

Comments: ~2.4-1 /;60 'j( 2. '0\12. U p", <., ,;:: 2 ~ {i" 2- _s 

Date of last revision 11/13/08 

OS834048 

Master Document StoragelFormslDatasheetslField Oatasheets 
CLIENT: SF 'VI 1"1 A 

LOCATION: ,- oJ ' ,,(>, .... 

DATE: \ 0 '::> 

RUN NO:;,- ~-r\<.. 0.1-' <O ,--;L 

OPERA TOR:=::----'b!.;2~_:_:____,,___---- . METER BOX NO: \J "-'l > 

METER ~H@: \ ~-'b METER Yd: '--'-,,,,,,,,;'1''',',,[('-----

STACK AREA, FT': '-\:' . \ ~I 

TRAVERSE POINTS, MIN/POINT: \ "'. ,~ 

~H= ·l X~P : 

Probe Condmon, pre/post test:+J..::"''----__ _ 

Silica Gel Expended, Y/N:_.:.:IV#/'----__ _ 

Filter Condition after Test: ;;p Check Weight: ___ -!:Ci7 ____ _ 

Meter ~P 

Point Time Volume, ft' in. H2O 

LJ I, \ "-\<; -:::':'4 . SSt; \ ' ~ 

'" \ ,,"'~ '1. Ci>;( ,cleU I ,'l--

~ , '-\0') '3 t,q, \,,\'D \ 1> ';, \,-\\5 ,,'1 _'=', 10".) \ ,'-:i. "- 1'-'\2'7 31',,, .:1.-.,,) \ . ~\ 

I 

,--\"" -:;';0 . S1~ I, () 

I v I 4,{ <; -:>"Il ·OS" 

N ~ \ -I'll'> 2111 "5,' ( .f) 

') ,LIS~ \tll ... ,:;, . .21 :.:; ;) . ''::::. 

'l \(';c/? '-U"I '916 ~. S 

3 f >1'1> ~i" '1 ,'Hr) '2. q, 1- I S 1'<, '-\ ? '\ 1 «.; l ·re 

I [0?. il t-:L '1 \ ,1')''5 ';)' '5 

L,) IS'iI"', Li SLI / ;)6(, 

Average: 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET 

AMBIENT TEMPERATURE: l 5 '" 

BAROMETRIC PRESSURE'-. ---;?''-c::'-, .. "',,;-;)(" -------

ASSUMED MOISTURE:_--:::,,"11~,.-_ ______ _ 

PITOT TUBE COEFF, Cpo 0' ltH 

PROBE 10 NOIMATERIAL-: --7.tj;l:""'2""''''---;SC:l-_I''''f.-:~-'(-'')--r(-:-",-;",-r2 

PROBE LENGTH: '1 \ 1 

NOZZLE 10 NO/ MATERIAL 21~-$C;i"'iL-+--"S;"-_____ _ 

NOZZLE DIAMETER: ",2. 7 ' 

FILTER NOITYPE: ~"''5~-'7"\ ,..rr\Cr\:=;c---"--------

PRE-TEST LEAK RATE:: ~'" CbS CFM@ 1 5' in. Hg. 

POST-TEST LEAK RATE: : CFM@ in. Hg. 

Imp. # Contents Post-Test - Pre-Test = Difference 

...L V.t')\':' 0 o (;(,J.. l~l, 1) 

z b£ \\.<..0 J>73,'1 L., s.~,S- -

3 J,{,'l & h'l ~'-lo,<1: -

L{ Seq- 0iJ.t?2 ~ olD '6 

t:>:s.. ll.. 2-0 L-i. I\.J C \2 \'\lSE I <Xl,o 

PITOT LEAK CHECK - PRE: v POST: 

CHAIN OF CUSTODY: SAMPLIE CUSTODIAN ----,/I--cA--

SAMPLER ~ 

SAMPLE CUSTODIAN Ak Total: ____________ _ 

~H Stack Probe Filter Imp. Out Meter Temp, OF Vacuum 02 Pstatic 

in. H2O Temp, OF Tern, OF Temp, OF Temp, OF In Out in. Hg. % in. H2O 

\ ,L. ':> ,,,\ 3- N V'<. «JIlt '3 0 t.,9 l.al.o .'-\ .,) d · " --,) .(i 

, 2,2- -"-1 ~ ~~l ,D '- ,f <: () 

\ ,\ 1'1\ LA '-j 10 b 'o () ·0 

i,·Sc, \~v C\ ',u S. . <" \ S'" 114 -1- 9~ VI 'S' lei n , 

\, 10 l~').- ,-\, [, '1 t,.'-i <\u 

\'1'6 1 '60 ' ( Gel ("-,, \.Ie) 

.i "1 ") 1 / g '-!-'7 7 (') c,'-i Lf L' 

;l...1") "7 e,o '-Ic- 1 0 (,,~I 4- -0 

. v"f '] 'f;0 ')1 V., (...'\ '" . .., 3- 0'6. 182- ~\ 6"-. 6'-1 .'> .:----, 

;(1') '1'&5 '?¢> V'l (,,? 5 -<..-

" tt " 

Comments: A/ute l\ ..... ""'4 J"""IT wa-kv' TN1"<'+-,~,,, ;,J ()"\/[tt-"'I~J f"..,,-,.,,-- CUJo,-v'i- 13'1t - iH;w 4> " ~I 

Date of last revision 11/13/08 0(vf I ~Y DS834048 Master Document StorageIForms\Datasheets\Field Datasheets 
8ella~ .. ~-.. - WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: '-'1" "" '" A 

LOCATION: ;';;'-\IT,''';] 

AMBIENTTEMPERATURE:,--________ _ _ Imp. # Contents Post-Test - Pre-Test = Difference 

DATE: 'I""~'? RUN NO:.;=-).I I'- - 1''''-==-iW.2 

OPERATOR: :0'7 

METERBOX~N~O~:~I~] W~L~~--------

METER~H@ : ________ ~~ ____ __ 

METER Yd: STACKARE~A~~F=Tr:--~N"~---------

TRAVERSE POINTS, IfI9I NT: ___ __ 

H= X~P : 

Probe conditiont!:pr Ipost tesl: 

Silica Gel Expan d, Y/N: ____ _ _ _ 

Filter Condition fter T esl: _ _ ___ _ _ 

BAROMETRIC PRESSURE: _______ _ _ _ _ 

ASSUMED MOISTURE: 

PITOT TUBE COEFF, C'--'p-: --------- - -

PROBE 10 NO/MATERIAL:. ____ ____ _ _ _ 

PROBE LENGTH: NOZZLEIDNO M~A~T=E=R~IA7L-:-- --- ----

NOZZLE DIAMETER: 

FILTER NOfTYPE: . ...-·_· ~------- ---

PRE-TEST LEIIK RATE:: "'A- CFM@ "' ;\,- in. Hg. 

POST-TEST LEAK RATE: : CFM@ in. Hg. 

PITOT LEAK CHECK - PRE: ,,(;( POST: -

CHAIN OF CUSTODY: SAMPLE CUSTODIAN --:-t±--

~ 

~ 

// 

7//---

Check Weighl: _ _ _______ _ "')pt:- SAMPLER s 7 . I' Cv>f., \ SAMPLE CUSTODIAN /.1>< Total: ___ _ ______ ______ _ 

Meter P H Stack Probe Filter Imp. Out Meter Temp, OF Vacuum 0, P. static 

Point I Time I Volume, ft' in. H,O in. H,O Temp, OF Temp, OF Te.mp., OF Temp, OF In lOut in. Hg. % in. H,O 

I e: "'S-,,'5" / . <;'0 (3'>1- 2 .° 1 

<; '),·1 S l'iSCo s ·.:,) 

"1 I \G'u I l.l.l}' 0100 I i· ~ \.1 \) I '1'6<0 I Ss I \C\ I c",'{: I 5·u , 11"'zu 1 "\l"\.loOO 1 \.() HO '1'81 I S,\ 1l:>9, ~'\: 1 ,';<5 

l I \\'?',--> 1 '-\~f:.,\"0 1 \, L I - \.,?"'L I "'Vi 1- '-, - 1 ------r- ~\---J~S I !Q'\ 1 6=21 

I I \ .. 'io 1 ,l1?J ,ooti 1 1 , '-- I 1·:'2- I 700 '7 \ 1 ~1.Ja.'" I_~Y) 

iJ 1 \ K O 1 \\o.,q .. f?Y< 

I C, II I \ ioSl I c.I"I"l .-I?,.~ \ ,~ \ ,,,\ ? .«;') (;'2- Cd :50 

5' I llul I Soiil. ),,'\0 i;-:' j . 'i .", ( B'-\ s:z, c' I.., ·U 

<./ I i 11[ Si 0. .. S (,) (.'1. ( 3'2 _ 1'8 (" s~ (" " ; I ".D.I I '),e; "(05 I • J.. , . '? 2 '1 "<--~ G \,,"\ 

1 1"01 S~" lW I ' G (I () --7Ci'5] I S-j c.. " I 11141 "5'52:,1 'D l c:,i 1 l..' 

J I I i ':'-1 1·")''.,'1N'., ,'2>1 ~2-. (" t)" 

Average: .Jl J.--

Comments: eQ

li 7... ;; 

Date of last revision 1/25/2013 Page 2... of 2- D5834049 Master Document 5toragei FormsiDatasheetsi Fieid Datasheets 
... Oel/aIJ.. 0_ .. _-........ 

WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: (:~t ",VI"", <-

LOCATION: 5.<,,-40,,~~{ C( k;-t- ;?. 

DATE: /-3)- /3 lJ2Q -'" 

RUN NO: .5 - .1 /:5,.,_ .-6'/"1 tff H"'X6 

OPERATOR: 6.6 METERBOX~N~0~:~)-~~ k~ ~'b---------

METER 6.H@: ) • S '7'" 

METER Yd: --iItl",_-"C;7j 71,!-,.-----------

STACK AREA. FT2: /" . 1'1 

TRAVERS E PO I NT"'S"'. -eM "'I N;';/:';:P"'O"'I N"'T",:c-.c>,",,,,=-t:;r-;:--

6.H= \.. \ X 6.P: ./ 

Probe Condition. pre/post test:..,.'--"'/'--__ 

Silica Gel Expanded. Y/N: __ "'!\\f)/L-____ _ 

Filter Condition after Test: ;7 

Check Weight: V 

Meter 

Point I Time I Volume, ft' 

;, 10 1 d'b,;,> 13",,,. '\sV 

. s 1 D'f.,'t'J ISS7.,s",o '-I oe.s~ 1 S(..;<'·0~') 

.:) 1 o"ln31 c;: '1 ( , 330 

2: 10 ql"J 1 S "l,USU 

r I w"l"-'? I "> '\ • . S't:> ~G>"\3.J1 \...00.23..0 

E (" 1 <.J "" '05 1 toco, 5'?U 

5 I <)cH'5 I (.,,"L .,::l" 

't 1 0' <;S ~ 1 /Q\ 11 ,:z. 'is '? I. ?Iilt> oS 1\.0 J.. '1 .;' 3c.-> 

7::. 1-,0\ ,<) Il, -,,1{ .~5'S' 

L 1 ; D 2.5-' ~'D; ~:>i' 

o i LO" S I c,s:, ,i'\"Ib 

Aver~: 

6.P 

in. H20 

CL'D 

:Z-6' 

.-" 

..s. 

!?, s "'\ .C? 

?..:O 

:;( , ;;I. 

~ 

\ .',3 

i) 

) .. ..;; 

AMBIENT TEMPERATURE: 1'1· ( BAROMETRIC PRESSURE-: --;;1;'~ ~X:~3~-------

ASSUMED MOISTURE: "110 

PITOT TUBE COEFF. C,-p-: ---,;e"'.<p!f:'1r --------

PROBE ID NO/MATERIAL: iJ t.<. \ ')111,';5 

NOZZLE ID NO/ MATERIAL:sn¥ e.5 

PROBE LENGTH: :"1 \ t' 

NOZZLE DIAMETER: If) ;-t: , 'I 

FILTER NO/TYPE: <;;, "" ::; 5'\"'1""1"""'-"9;'--''-'-- ---- -- PRE-TEST LEAK RATE:: <O,Do'> CFM@ 15 in. Hg. 

POST-TEST LEAK RATE: : CFM@ in. Hg. 

PITOT LEAK CHECK - PRE: v POST: ____ _ 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN I>rI>,. 

6.H 

in, H20 

:tr1 ., 

;2... "IT 

;(. S.." 

:l.. 1.~ 

'J.-..?l. 

;t -<b(" 

p.. . d-.O 

;;2"'-1),, 

;{..-L{:J.. 

IA-:' 

.:A..cl 

,'lS 

Stack 

Temp, OF 

'1 'I'-\. -:1,.:: 

1"1 (p 

..":l'l ~ ,'b0 

'1e..o 

-'1 \Q 

TIS 

1'3 

'l'!1 

'1'bV 

Iqo~ 

SAMPLER ""5 

SAMPLE CUSTODIAN K:.kProbe 

Temp. OF 

I-' )P< 

/..-

Filter 

Temp, OF 

~l!,-

v 

Imp, Out 

Temp. OF 

5'--1 

,i.f'-\ 

'-tie 

'fS' 

'--V<> 

<{'l 

'::>D 

't'?) 

<;1 

s;>... 

Se) 

S>! 

Imp, # Contents Post-Test - Pre-Test = Difference 

(J..t: IJ ,..c q$l~ t,b9z 

;".. 'I crZ[, q 1'11 1 

3 Aif- ~5~q w3'J...« 

Ii 6~,- ~fn , '1 J'-I/. 7 

/. '"",,/ <1. i' --x..-- - 100 

Total: 

Meter Temp. OF Vacuum 0 2 P. static 

In Out in. HQ. % in. H2O 

t. L . 4>(., 'l>- , "" r3.-q~t -q~ /;;.'b .(..-0 

1"1 ,0 (.,-ri 

'2> 1?, 10·6 

'ed '1'-\ !: ... .-" 

'211 ,s lou 

bD 1'6 ~, ') 

1> 1'6 l.,. -O 

~ 1'1 (,..- tl 

R~ '&l Co -tJ 

e \'30 L, -a 

Bi '60 ~O 

.J;.-

Comments: ____________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page lof L 

DS834049 

Master Document StoragelFormsl DatasheetslField Datasheets 
WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: GtC/YI,.," 

LOCATION: , '" <oTl N c.vDATE: 1;'1 L3 

RUN NO: S- :l' '7Tk" 'I '" " I ~D 3> 

OPERATOR: s.j. METERBO ~N~0~~~ ?~--------

METER @: _____ --,<-___ _ 

METER Yd: STACKARE:A~~F=TT:- ~- ---

TRAVERSE POINTS, M IPOINT: __ _ 

~ _____ X ~P: 

Probe Condition, prel ost tesl: _____ _ 

Silica Gel Expanded, YIN: 

Filter Condition after Tesl:-----------

Check Weighl: __________________ __ 

Meter t>P 

Point Time Volume, ft3 in, H2O 

,J 10 '0o,\. cs" A'1b \,3 

':> \ ."" U ,O l-\C \ ,4 

"I \<>51 l, i.'" :3 0 U \ ,I-

'J. \ \01 t.., S- ,500 L 'l 

"- tIll (.'&A, '600 \,~ 

\ \ 121 (pcI " ~'1J \' '2-

0 \\3'1 t.'\, ,S,-<) , 

W ~ In (.q",':> loS t , '1\ 

'? \ I 'I ,0"1·, 30 \,:",> 

'-\ \ \ S 1 vi '11. D L':l 

) 1'1. 0 \1'1 "\\0 \, ;-<. 

1- \2.1 ' "1 :u. ,'{& 0 i,( 

1 ..1.'1.:2_" ~:,.o30 10 

D 1 '2. "':CI 'T,,-t.{ .. i U 

Average: 

AMBIENT TEMPERATURE: c 

BAROMETRIC PRESSURE: Z Imp, # Contents Post-Test - Pre-Test ~ Difference 

ASSUMED MOISTURE: Z 

PITOT TUBE COEFF, Cp:__ ;> 

PROBE ID NO/MATERIAL: _ _ --;?'c"-______ _ 

PROBE LENGTH: // 

NOZZLE ID NOI MATERIAL: 7 

NOZZLE DIAMETER:_---;,'-r ___ ______ _ 

FILTER NOfTYPE: ,/ 

PRE-TEST LEAK R"'A"'T:;:E"':'''' :------;C"'F:;M7:@O;;-- ---:i-n,""H""g-,-

POST-TEST LEAK RATE: : <O,a,-LCFM@ ,,.;- in, Hg, 

PITOT LEAK CHECK - PRE: POST: ~ 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN /1.-,1\-

S. .-;:- rc SAMPLER 55 

{?ev,g I SAMPLE CUSTODIAN---,A21A,,--_ Total: ____ __________ _ _ 

H Stack Probe Filter Imp, Out Meter Temp, OF Vacuum 0 2 p, static 

in, H2O Temp, OF Temp, OF Temp, OF Temp, OF In Out in, Hg, % in, H2O 

\ ,'-\3 11'-\"' \ fA'AI> "-'A tv I ,C>. "'''1 "<fa "19 "t,n \q, -< <10-,2; \ 

\ ,s- ,,(0 ;';1.. '0_0 1'5 '1 ·0 

l,3 111 v'S 'tJ\ 'l.B ~ ·0 

I ,j) < '1 'CD 53 ~I 11 ~ ~/'l 

18Y '16\ £''t r'l\ '1.l .;) 

I ,'?>:l iP:P- ,=>C,p <£.1 "11 ,,, -0 

L'-':;' '1<8 ':>y,. "1'1 "1 't') S·U 

t ,'-\-', 1 ') b:S ~ -19, "\,0 

\ -5'-1 l l " s, '00 1 1', 5 ·/) 

l -::>, ).. -, fb\ S'"<) "0-1 1 p, ~<J 

i ,2- 1.'D 2- 5'1 ~? [1 S,., 

I, \ 0 1 '0':') s'i 't>3 &0 S·D 

f..-' 

~ ~ 

, 

v 

Comments: ____________________________________________________________________________________________________________________________ __ 

Date of last revision 1/25/2013 Page '2- of "2---

05834049 

Master Document Storagel FormslDatasheetslField Datasheets 
WET CHEMICAL SAMPLING SYSTEM DATA AND WORKSHEET - STANDARD 

CLIENT: rJ.-.v.-,, ~,, __ LOCATION: .6" ±-; (c <f t-<N ·t 2-

DATE: .,.)- {-- r<, 

RUN NO: :+ ., -- (J'""]J;T...<lF - fJ/Y, 

OPERATOR: I,'~ ( oS ·- -:.. h _ ~ ... -- A 

METER BOX NO:"':,,rr - --""'<l""-="'-=£'-___ _ 

METER .:.H@:_-"I.-"\$''''k7-=-:-___ _ 

METER Yd: O. q fi< 

STACK AREA, FT': (':n i'j' 

TRAVE13SE POINTS, MIN/POINT: Nt.),.-

"H= -*- X "P: -:-7 

Probe Condition, pre/post test~: ,/ 

Silica Gel Expanded, YIN: __ ./:.' 

Filter Condition after Test 7 

Check Weight ____ -''-

Meter " p 

Point Time Volume. ft3 in. H,O 

'J () 1)'-' 'I'i l"i¢O 

r"1 IQCD 

~erage: 

AMBIENT TEMPERATURE: e& 

BAROMETRIC PRESSURE-: --,7-:';-1.*-0",------

ASSUMED MOISTURE::_--;;cnc'1f-/':.:.· ; ____ _ 

PITOT TUBE COEFF, Cp: o4~ ( 

PROBE 10 NO/MATERIAL: tf-,!(., $1'i pG I :;, G Ss 

PROBE LENGTH: 7' , NOZZLE 10 NO/ MATE RIAL: -c:;--"':"''-'S~ _ _____ _ 

NOZZLE DIAMETER: o . •. x S 

FILTER NOfTYPE: .50" - 17'" I 

PRE-TEST LEAK RATE: : 40.QO) CFM@ 15"" in. Hg . 

POST-TEST LEAK RATE: : "',}- CFM@ tJlt in. Hg. 

PITOT LEAK CHECK - PRE: ...- POST: ,;ft 

CHAIN OF CUSTODY: SAMPLE CUSTODIAN !\f=-- SAMPLER ~" 

SAMPLE CUSTODIAN Ak"'" 

"H Stack Probe Filter Imp. Out 

in. H,O Temp. OF Temp, OF Temp, OF Temp, OF 

r , / 1 /1 ) 

/ / 1./ ______ 7 / 

/I / 11/ fl /\ /\ II 

/ IL I .J ( 

If , f' J 

U/ 

\ 

Imp. # Contents Post-Test - Pre-Test = Difference 

0]: I·h' ]8S.1 ~f!5: Z 

"" '( 750.0 

3 .1)'1'\, ~33'1 

" ,2 G--- ,f"?;l-I 

J.... i.u; e·~ "'" _ t CD 

Total: _ ______ • __ _ 

Meter Temp. OF Vacuum 0, P. static I 

In Out in. Hg. % in. H,O 

I 

Comments: ____ ___ _________________________ _______________________ _ 

Date of last revision 1125/2013 Page __ of __ 

DS834049 

Master Document StoragelFormslDatasheetslField Datasheets 
DcllaJ1 

PARTICULATE 

SCAQMD 5.1, WET IMPINGEMENT 

Ga.""", ... 1/:rO/IJ 

Project # 

ClienVLocation 

Sample Location 

Test # 

Un; ~ Water Blank mg/ml 

Sample Date 

Analysis Date 

5l 81.¥(· P/II,-/ctrl MeCl, Blank mg/ml Analyst Initials 

• 

Item Number 

1. Glass Fiber Filter :;'''5"- (Backup Filter) 

) 1(f' 

2. Insoluble Solids Filter 5S-

/790 

3. Impingers and Probe 

Catches 1l2(,jZ 

a. Water Fraction 

b. Organic Extraction 1/2. c.(.. 125 ml MeCI2 

(5 x 25 ml) 

Dellaf1 

"'---

Date of last revision 11/13/08 

Final Tare Gain Al iquot Net Gain Blank based 

Weight Weight Weight Correction (mg/Sample) on Total 

(g) (g) (mg) (ml/ml) Volume (mg) 

O.10'{O o .f{,~rl. G·U 0,0 ------------- -----------------

rJ. tb')] D./~3{\ 0 ·0 0,0 --------------- -----------------

75"0 

19.5('1£ 2'1.S13S" "l.o :..--- Lj.o 1~ 6 ·3 

1~ ~81) ~ ".,&'80 

15() 6 0.0 D·D .0 --- 75"0 

Total Particulate = _--'L(~ . .:::D ____ __'m'_"g"_ 

Method of Sample Prep/Notes 

DS834012 

Master Document StoragelFormslDatasheetslLab Forms 
DlJllai1. 

PARTICULATE 

SCAQMD 5.1, WET IMPINGEMENT 

Project # 

ClienVLocation C;"'M.:""'" 

Sample Location Un; t. 1:. Water Blank mg/ml 

Sample Date 

Analysis Date 

Test # 5 1:/#/(- P/II-/W-1.MeCI, Blank mg/ml Analyst Initials • 

Item Number 

1. Glass Fiber Filter g,- (Backup Filter) (7-(9 

2. Insoluble Solids Filter S$-

ir9( 

3. Impingers and Probe 

Catches 112(;.7 

a. Water Fraction 

b. Organic Extraction 

125 ml MeCI2 I {7.,r,&" 

(5 x 25 ml) 

Date of last revision 11/13/08 

Final Tare Gain Aliquot Net Gain Blank based 

Weight Weight Weight Correction (mg/Sample) on Total 

(g) (g) (mg) (mUml) Volume (mg) 

O.lb 3'3 o.f('3f' 6,0 --------------- 0.0 ------_.---------

0 .((,")0 0./(;32.. 6,0 --------------- 0·0 -----------------

1'1.(,002.. 2'1· ~~I 2. \ 110 

1/0 '2.. I 0 ,3 

2ct.j(,t,2- 2'1·/('(.3 0·0 JfJ2- 0 · 0 0·0 710 

Total Particulate = __ 2_.-'I ____ -'m"'9ilMethod of SamQle Prep/Notes 

DS834012 

Master Document StoragelFormslDatasheetslLab Forms 
D/Jlla~ 

PARTICULATE 

SCAQMD 5.1, WET IMPINGEMENT 

Project # 

Client/Location C,""I'kM'" 

Sample Location UI); r. Water Blank mg/ml 

Sample Date 

Analysis Date 

Analyst Initials 

"Zf //.3 

Test # 5l /$0.1(- P/w"-Itx>-) MeCl, Blank mg/ml • 

Item Number 

1. Glass Fiber Filter 5S- (Backup Filter) 113'7 

2. Insoluble Solids Filter 5S-

/7'{ 'I... 

3. Impingers and Probe 

Catches tin) 

a. Water Fraction 

b. Organic Extraction 

125 ml MeCI2 {{ITo 

(5 x 25 ml) 

Date of last revision 11/13/08 

Final Tare Gain Aliquot Net Gain Blank based 

W~tt W~tt Weight Correction (mg/Sample) on Total 

(mil) (ml/ml) Volume (mQ) 

O,\"I~ 0./(,20 0.0 D·O -------------- ---._----------

O.lb'W O./(' ZO 6,0 0 · 0 --------------. -----------------

2.'i.'1S2.~ 1.'1.%'63 z· 2.. ~ 

10K' 

1~ 2· 2. 0.3 

::/'1-3t>i'J Z'I. ~(,<; (>.,,( J55. 

:{b,f 

o.l.J 0 ·0 

Total Particulate = _-=='2:..' ''''c;. ____ ...:m.:..:....9 

Method of Sample Prep/Notes 

DS834012 

Master Document StoragelFormslDatasheetslLab Forms 
8811aJ1. 

PARTICULATE 

SCAQMD 5.1, WET IMPINGEMENT 

Project # 

Client/Location 

Sample Location 

Test# 52161.1(- P/M,. fl3 

• 

Item Number 

1. Glass Fiber Filter SS- (Backup Filter) 

17{j/ 

2. Insoluble Solids Filter 55'-

/1'6/ 

3. Impingers and Probe 

Catches I [1..5 'i 

a. Water Fraction 

b. Organic Extraction 

125 ml MeCI2 1(2,5~ 

(5 x 25 ml) 

DI I{~ 0 61CN\. K /I]. (.0 

NoLC.! 1.... 8l Vv\ I< 1{2.(,\ 

Deltal1 "'--.- Date of last revision 11/13/08 

Water Blank mglml 

MeCl, Blank mglml 

Final Tare 

Weight 

(Q) 

Weight 

Jg) 

0.\{'1.6 0./(''27-

O.u,;,3 ,~ 

() . It; 33 

Z9.'io3J ).If. 'i <> j1 

2'1. Q'E3 2C,.IIH~ 

~"rIl~Y l.'i.jl'l1-

1G·'~O :z.,. ... HI 

0.01>0</ 

6. "'<>00 

Gain 

Weight 

(mol 

0 · 0 

Sample Date 

Analysis Date 

Analyst Initials 

Aliquot Net Gain 

Correction (mg/Sample) 

(ml/ml) 

0·0 ----------------

0·0 -------------- Q,O 

(;.() 

/92-

19l 0-0 

(;·0 !Jt /92-. 6 ,0 

o. { ~ 150 

ZSO 

0 ·0 ~ 

Blank based 

on Total 

Volume (mg) 

-----------------

--------------

o. { 

0 . 0 

Total Particulate = 6 .0 mg --------------~~ 

Method of Sample Prep/Notes 

DS834012 

Master Document StoragelFormslDatasheetslLab Forms 
CPV SENTINEL UNIT 2 

PARTICULATE TEST 

STACK O2• CO2 DATA 

Test #: S-2/STK-PM-50-1 

Date: 2/1/2013 

Time: 14:14 18:25 

Load: 55MW 

O2 CO2 

Range 20 10 

Cal Gas 9.98 4.96 

Analyzer Zero 0.10 0.14 

Analyzer Span 10.11 5.25 

Pre-Bias Zero 0.21 0.19 

Pre-Bias Span 10.11 5.24 

Post-Bias Zero 0.23 0.10 

Post-Bias Span 10.17 5.11 

Average Bias Zero 0.22 0.15 

Average Bias Span 10.14 5.18 

Pre-test zero bias 0.5% 0.6% 

Pre-test span bias 0.0% 0.0% 

Post-test zero bias 0.7% -0.4% 

Post-test span bias 0.3% -1.4% 

Zero Drift 0. 1% -0.9% 

Span Drift 0.3% -1.3% 

Test Results (from data logger average) 

Average 14.42 4.01 

Cal Corrected 14.29 3.80 

O2 CO2 

Date Time % % 

2/1/2013 14:15:00 14.415 4.079 

2/1/2013 14:16:00 14.388 4.098 

2/1 /2013 14:17:00 14.368 4.11 

2/1/2013 14:18:00 14.372 4.109 

2/1/2013 14:19:00 14.395 4.099 

2/1/2013 14:20:00 14.379 4.109 

2/1 /2013 14:21 :00 14.364 4.112 

2/1/2013 14:22:00 14.373 4.106 

2/1/2013 14:23:00 14.397 4.095 

2/1/2013 14:24:00 14.394 4.098 
2/1/2013 14:25:00 14.383 4.104 

2/1/2013 14:26:00 14.368 4.11 

2/1/2013 14:27:00 14.368 4.108 

2/1/2013 14:28:00 14.363 4.113 

2/1/2013 14:29:00 14.363 4.111 

2/1/2013 14:30:00 14.372 4.101 

2/1 /2013 14:31 :00 14.366 4.103 

2/1/2013 14:32:00 14.38 4.093 

2/1/2013 14:33:00 14.371 4.098 

2/1/2013 14:34:00 14.382 4.087 

2/1/2013 14:35:00 14.359 4.097 

2/1/2013 14:36:00 14.367 4.088 

2/1 /2013 14:38:00 14.411 4.071 

2/1/2013 14:39:00 14.38 4.077 

2/1/2013 14:40:00 14.38 4.077 

2/1/2013 14:41:00 14.382 4.076 

2/1/2013 14:42:00 14.385 4.076 

2/1/2013 14:43:00 14.392 4.072 

2/1/2013 14:44:00 14.385 4.074 

2/1 /2013 14:45:00 14.387 4.075 

2/1/2013 14:46:00 14.391 4.072 

2/1/2013 14:47:00 14.375 4.083 

2/1/2013 14:48:00 14.377 4.081 

2/1/2013 14:49:00 14.368 4.082 

2/1/2013 14:50:00 14.341 4.098 

2/1/2013 14:51 :00 14.306 4.123 

2/1/2013 14:52:00 14.308 4.119 

2/1/2013 14:53:00 14.299 4.124 

2/1/2013 14:54:00 14.304 4.124 

2/1/2013 14:57:00 14.346 4.086 

2/1/2013 14:58:00 14.343 4.094 

2/1/2013 14:59:00 14.336 4.102 

2/1/2013 15:00:00 14.344 4.095 

2/1/2013 15:01 :00 14.344 4.096 

2/1/2013 15:02:00 14.35 4.094 

2/1 /2013 15:03:00 14.345 4.098 

2/1/2013 15:04:00 14.342 4.104 

2/1/2013 15:05:00 14.349 4.093 

2/1/2013 15:06:00 14.345 4.1 01 

2/1/2013 15:07:00 14.344 4.1 

2/1/2013 15:08:00 14.345 4.097 

2/1/2013 15:09:00 14.348 4.097 

2/1/2013 15:10:00 14.342 4.106 

2/1 /2013 15:1 1:00 14.342 4. 106 

2/1/2013 15:12:00 14.348 4.099 

2/1/2013 15:13:00 14.349 4.096 

2/1/2013 15:14:00 14.344 4.101 

2/1/2013 15:15:00 14.346 4.1 

2/1/2013 15:16:00 14.345 4.103 

2/1/2013 15:17:00 14.455 4.047 

2/1/2013 15:20:00 14.399 4.069 
2/1/2013 15:21 :00 14.398 4.071 

2/1/2013 15:22:00 14.391 4.077 

2/1/2013 15:23:00 14.39 4.075 

2/1/2013 15:24:00 14.392 4.073 

2/1/2013 15:25:00 14.398 4.07 

2/1/2013 15:26:00 14.421 4.057 

2/1/2013 15:27:00 14.434 4.053 

2/1/2013 15:28:00 14.427 4.057 

2/1/2013 15:29:00 14.44 4.05 

2/1/2013 15:30:00 14.427 4.055 

2/1/2013 15:31 :00 14.437 4.048 

2/1/2013 15:32:00 14.44 4.043 

2/1/2013 15:33:00 14.462 4.031 

2/1/2013 15:34:00 14.452 4.037 

2/1/2013 15:35:00 14.465 4.03 

2/1/2013 15:36:00 14.454 4.037 

2/1/2013 15:37:00 14.449 4.039 

2/1/2013 15:52:00 14.342 4.003 

2/1/2013 15:53:00 14.398 4.051 

2/1 /2013 15:54:00 14.396 4.056 

2/1 /2013 15:55:00 14.389 4.062 

2/1/2013 15:56:00 14.407 4.054 

2/1/2013 15:57:00 14.4 4.06 

2/1/2013 15:58:00 14.412 4.056 

2/1/2013 15:59:00 14.439 4.039 

2/1/2013 16:00:00 14.466 4.025 

2/1/2013 16:01 :00 14.474 4.02 

2/1/2013 16:02:00 14.46 4.028 

2/1/2013 16:03:00 14.452 4.03 

2/1/2013 16:04:00 14.453 4.027 

2/1/2013 16:05:00 14.473 4.017 

2/1/2013 16:06:00 14.464 4.019 

2/1/2013 16:07:00 14.501 4.003 

2/1/2013 16:08:00 14.474 4.014 

2/1/2013 16:09:00 14.462 4.018 

2/1/2013 16:12:00 14.508 4.036 

2/1/2013 16:1 3:00 14.364 4.068 

2/1/2013 16:14:00 14.367 4.068 

2/1/2013 16:15:00 14.356 4.074 

2/1/2013 16:16:00 14.361 4.071 

2/1/2013 16:17:00 14.349 4.079 

2/1/2013 16:18:00 14.344 4.085 

2/1/2013 16:19:00 14.345 4.08 

2/1/2013 16:20:00 14.343 4.084 

2/1/2013 16:21 :00 14.353 4.072 

2/1/2013 16:22:00 14.353 4.077 

2/1/2013 16:23:00 14.317 4.106 

2/1/2013 16:24:00 14.319 4.103 

2/1/2013 16:25:00 14.326 4.099 

2/1/2013 16:26:00 14.318 4.104 

2/1/2013 16:27:00 14.323 4.096 

2/1/2013 16:28:00 14.323 4.1 
2/1/2013 16:30:00 14.388 4.052 

2/1/2013 16:31 :00 14.38 4.052 

2/1/2013 16:32:00 14.374 4.055 

2/1/2013 16:33:00 14.36 4.06 

2/1/2013 16:34:00 14.376 4.052 

2/1/2013 16:35:00 14.383 4.046 

2/1/2013 16:36:00 14.367 4.053 

2/1/2013 16:37:00 14.37 4.049 

2/1/2013 16:38:00 14.384 4.039 

2/1/2013 16:39:00 14.4 4.028 

2/1/2013 16:40:00 14.4 4.025 

2/1/2013 16:41 :00 14.385 4.03 

2/1/2013 16:42:00 14.37 4.04 

2/1/2013 16:43:00 14.367 4.039 

2/1/2013 16:44:00 14.379 4.031 

2/1/2013 16:45:00 14.347 4.049 

2/1/2013 16:46:00 14.369 4.03 

2/1/2013 16:47:00 14.369 4.029 

2/1/2013 16:48:00 14.365 4.03 

2/1/2013 16:49:00 14.36 4.032 

2/1/2013 16:50:00 14.347 4.041 

2/1/2013 16:53:00 14.453 3.973 

2/1 /2013 16:54:00 14.441 3.977 

2/1 /2013 16:55:00 14.43 3.985 

2/1/2013 16:56:00 14.435 3.981 

2/1/2013 16:57:00 14.44 3.978 

2/1/2013 16:58:00 14.443 3.974 

2/1/2013 16:59:00 14.439 3.978 

2/1/2013 17:00:00 14.444 3.974 

2/1/2013 17:01 :00 14.479 3.953 

2/1/2013 17:02:00 14.462 3.959 

2/1/2013 17:03:00 14.471 3.952 

2/1/2013 17:04:00 14.463 3.951 

2/1/2013 17:05:00 14.456 3.953 

2/1/2013 17:06:00 14.465 3.948 

2/1/2013 17:07:00 14.484 3.936 

2/1 /2013 17:08:00 14.481 3.936 

2/1/2013 17:09:00 14.484 3.933 

2/1/2013 17:10:00 14.486 3.932 

2/1/2013 17:11 :00 14.451 3.945 

2/1/2013 17:12:00 14.456 3.944 

2/1/2013 17:30:00 14.359 3.845 

2/1/2013 17:31 :00 14.382 3.866 

2/1/2013 17:32:00 14.425 3.905 

2/1/2013 17:33:00 14.458 3.899 

2/1/2013 17:34:00 14.445 3.906 

2/1/2013 17:35:00 14.477 3.893 

2/1/2013 17:36:00 14.482 3.893 

2/1/2013 17:37:00 14.485 3.892 

2/1/2013 17:38:00 14.473 3.893 

2/1/2013 17:39:00 14.483 3.892 
2/1/2013 17:40:00 14.477 3.892 

2/1/2013 17:41 :00 14.502 3.878 

2/1/2013 17:42:00 14.51 3.874 

2/1/2013 17:43:00 14.514 3.87 

2/1/2013 17:44:00 14.508 3.871 

2/1/2013 17:45:00 14.519 3.864 

2/1/2013 17:46:00 14.514 3.864 

2/1/2013 17:47:00 14.493 3.872 

2/1/2013 17:48:00 14.502 3.869 

2/1/2013 17:49:00 14.51 3.866 

2/1/2013 17:50:00 14.515 3.861 

2/1/2013 17:51 :00 14.501 3.866 

2/1/2013 17:52:00 14.5 3.865 

2/1/201 3 17:53:00 14.512 3.855 

2/1/2013 17:54:00 14.522 3.845 

2/1/2013 17:55:00 14.524 3.84 

2/1/2013 17:56:00 14.53 3.832 

2/1/2013 17:57:00 14.525 3.831 

2/1/2013 17:58:00 14.527 3.827 

2/1/2013 17:59:00 14.519 3.831 

2/1 /2013 18:00:00 14.519 3.825 

2/1/2013 18:01 :00 14.53 3.816 

2/1/2013 18:02:00 14.528 3.81 

2/1/2013 18:03:00 14.544 3.797 

2/1 /2013 18:04:00 14.545 3.795 

2/1/2013 18:05:00 14.544 3.795 

2/1/2013 18:06:00 14.537 3.799 

2/1/2013 18:07:00 14.539 3.796 

2/1/2013 18:08:00 14.541 3.795 

2/1/2013 18:09:00 14.53 3.8 

2/1/2013 18:10:00 14.54 3.793 

2/1/2013 18:11 :00 14.529 3.798 

2/1/2013 18:12:00 14.543 3.789 

2/1/2013 18:13:00 14.55 3.782 

2/1/2013 18:14:00 14.551 3.779 

2/1/2013 18:15:00 14.552 3.776 

2/1/2013 18:16:00 14.552 3.776 

2/1/2013 18:17:00 14.538 3.784 

Average 14.42 4.01 
Test #: 

Date: 

Time: 

Load: 

CPV SENTINEL UNIT 2 

PARTICULATE TEST 

STACK O2 • CO2 DATA 

S-2/STK-PM-75-1 

2/1/2013 

8:11 13:22 

80MW 

O2 

Range 20 

Cal Gas 9.98 

Analyzer Zero 0.1 0 

Analyzer Span 10.19 

Pre-Bias Zero 0.12 

Pre-Bias Span 10.04 

Post-Bias Zero 0.20 

Post-Bias Span 10.12 

Average Bias Zero 0.16 

Average Bias Span 10.08 

Pre-test zero bias 0.1% 

Pre-test span bias -0.8% 

Post-test zero bias 0.5% 

Post-test span bias -0.4% 

Zero Drift 0.4% 

Span Drift 0.4% 

CO2 

10 

4.96 

-0.02 

5.05 

0.03 

5.08 

0.25 

5.32 

0.14 

5.20 

0.5% 

0.3% 

2.6% 

2.7% 

2.2% 

2.4% 

Test Results (from data logger average) 

Average 13.43 4.49 

Cal Corrected 13.35 4.26 

O2 CO2 

Date Time % % 

2/1/2013 8:25:00 13.431 4.306 

2/1/2013 8:26:00 13.474 4.292 

2/1/2013 8:27:00 13.496 4.287 

2/1/2013 8:28:00 13.478 4.304 

2/1/2013 8:29:00 13.427 4.339 

2/1/201 3 8:30:00 13.422 4.346 

2/1/2013 8:31 :00 13.363 4.385 

2/1/2013 8:32:00 13.377 4.38 

2/1 /2013 8:33:00 13.307 4.421 

2/1/2013 8:34:00 13.333 4.412 
2/1/2013 8:35:00 13.319 4.425 

2/1/2013 8:40:00 13.268 4.428 

2/1/2013 8:41 :00 13.298 4.445 

2/1/2013 8:42:00 13.307 4.45 

2/1/2013 8:43:00 13.319 4.452 

2/1/2013 8:44:00 13.314 4.459 

2/1/2013 8:45:00 13.329 4.458 

2/1/2013 8:46:00 13.336 4.457 

2/1/2013 8:47:00 13.343 4.459 

2/1/2013 8:48:00 13.344 4.463 

2/1/2013 8:49:00 13.349 4.466 

2/1/2013 8:50:00 13.353 4.467 

2/1/2013 8:51 :00 13.366 4.466 

2/1/2013 8:52:00 13.366 4.469 

2/1/2013 8:53:00 13.37 4.47 

2/1/2013 8:54:00 13.37 4.473 

2/1/2013 8:55:00 13.372 4.476 

2/1/2013 8:56:00 13.38 4.472 

2/1 /2013 8:57:00 13.39 4.466 

2/1/2013 8:58:00 13.4 4.463 

2/1/2013 8:59:00 13.404 4.462 

2/1/2013 9:00:00 13.403 4.463 

2/1/2013 9:01 :00 13.411 4.462 

2/1/2013 9:02:00 13.418 4.458 

2/1/2013 9:03:00 13.413 4.461 

2/1/2013 9:04:00 13.413 4.464 

2/1/2013 9:05:00 13.425 4.456 

2/1 /2013 9:06:00 13.429 4.454 

2/1/2013 9:07:00 13.432 4.448 

2/1/2013 9:08:00 13.437 4.448 

2/1/2013 9:09:00 13.43 4.452 

2/1 /2013 9:10:00 13.432 4.453 

2/1/2013 9:11:00 13.438 4.451 

2/1/2013 9:12:00 13.45 4.449 

2/1/2013 9:13:00 13.437 4.455 

2/1/2013 9:14:00 13.445 4.453 

2/1/2013 9:15:00 13.45 4.453 

2/1/2013 9:16:00 13.476 4.445 

2/1/2013 9:17:00 13.486 4.443 

2/1/2013 9:18:00 13.492 4.441 

2/1/2013 9:19:00 13.493 4.444 

2/1/2013 9:20:00 13.494 4.445 

2/1/2013 9:21 :00 13.482 4.451 

2/1/2013 9:22:00 13.483 4.454 

2/1 /2013 9:23:00 13.478 4.457 

2/1/2013 9:24:00 13.468 4.461 

2/1 /2013 9:25:00 13.471 4.461 

2/1/2013 9:28:00 13.626 4.359 

2/1/2013 9:29:00 13.624 4.357 

2/1/2013 9:30:00 13.627 4.356 

2/1/2013 9:31 :00 13.64 4.348 

2/1/2013 9:32:00 13.63 4.351 
2/1/2013 9:33:00 13.521 4.419 

2/1/2013 9:34:00 13.492 4.436 

2/1/2013 9:35:00 13.497 4.432 

2/1/2013 9:36:00 13.467 4.449 

2/1 /2013 9:37:00 13.436 4.462 

2/1/2013 9:38:00 13.427 4.472 

2/1/2013 9:39:00 13.43 4.471 

2/1/2013 9:40:00 13.43 4.468 

2/1/2013 9:41 :00 13.427 4.471 

2/1 /2013 9:42:00 13.428 4.471 

2/1/2013 9:45:00 13.463 4.449 

2/1/2013 9:46:00 13.473 4.446 

2/1 /2013 9:47:00 13.491 4.435 

2/1/2013 9:48:00 13.508 4.426 

2/1/2013 9:49:00 13.497 4.428 

2/1/2013 9:50:00 13.449 4.462 

2/1/2013 9:51 :00 13.421 4.482 

2/1/2013 9:52:00 13.414 4.485 

2/1/2013 9:53:00 13.406 4.491 

2/1/2013 9:54:00 13.417 4.484 

2/1/2013 9:55:00 13.424 4.479 

2/1/2013 9:56:00 13.448 4.463 

2/1/2013 9:57:00 13.429 4.475 

2/1/2013 9:58:00 13.424 4.48 

2/1/2013 9:59:00 13.422 4.484 

2/1/2013 10:19:00 13.489 4.479 

2/1/2013 10:20:00 13.492 4.48 

2/1/2013 10:21 :00 13.493 4.483 

2/1/2013 10:22:00 13.477 4.489 

2/1/2013 10:23:00 13.475 4.492 

2/1/2013 10:24:00 13.478 4.489 

2/1/2013 10:25:00 13.475 4.488 

2/1/2013 10:26:00 13.49 4.479 

2/1/2013 10:27:00 13.488 4.481 

2/1/2013 10:28:00 13.49 4.481 

2/1/2013 10:29:00 13.499 4.477 

2/1/2013 10:30:00 13.487 4.482 

2/1 /2013 10:31 :00 13.479 4.488 

2/1/2013 10:32:00 13.468 4.499 

2/1/2013 10:33:00 13.473 4.496 

2/1/2013 10:34:00 13.469 4.497 

2/1/2013 10:35:00 13.474 4.493 

2/1/2013 10:36:00 13.059 4.287 

2/1/2013 11 :05:00 13.44 4.505 

2/1/2013 11 :06:00 13.44 4.505 

2/1/2013 11 :07:00 13.433 4.516 

2/1/2013 11 :08:00 13.432 4.519 

2/1/2013 11 :09:00 13.44 4.512 

2/1/2013 11:10:00 13.45 4.51 

2/1/2013 11:11 :00 13.441 4.515 

2/1/2013 11 :12:00 13.438 4.517 
2/1 /2013 11 :13:00 13.445 4.513 

2/1/2013 11:14:00 13.452 4.513 

2/1/2013 11:15:00 13.45 4.515 

2/1/2013 11:16:00 13.444 4.52 

2/1/2013 11:17:00 13.437 4.524 

2/1/2013 11:18:00 13.44 4.522 

2/1/2013 11 :19:00 13.437 4.521 

2/1/2013 11 :20:00 13.438 4.521 

2/1/2013 11 :23:00 13.423 4.531 

2/1/2013 11 :24:00 13.425 4.532 

2/1/2013 11 :25:00 13.418 4.537 

2/1/2013 11 :26:00 13.416 4.537 

2/1/2013 11 :27:00 13.41 4.543 

2/1/2013 11 :28:00 13.406 4.545 

2/1/2013 11 :29:00 13.405 4.547 

2/1/2013 11 :30:00 13.404 4.545 

2/1/2013 11 :31:00 13.407 4.541 

2/1/2013 11 :32:00 13.418 4.534 

2/1/2013 11 :33:00 13.409 4.541 

2/1/2013 11 :34:00 13.405 4.543 

2/1/2013 11 :35:00 13.407 4.543 

2/1/2013 11 :36:00 13.412 4.543 

2/1/2013 11 :37:00 13.413 4.543 

2/1/2013 11 :38:00 13.41 4.546 

2/1/2013 11 :41 :00 13.433 4.53 

2/1/2013 11 :42:00 13.423 4.542 

2/1/2013 11 :43:00 13.428 4.537 

2/1/20 13 11 :44:00 13.423 4.543 

2/1 /2013 11 :45:00 13.422 4.546 

2/1/2013 11 :46:00 13.428 4.539 

2/1/2013 11:47:00 13.427 4.539 

2/1/2013 11 :48:00 13.43 4.539 

2/1/2013 11 :49:00 13.431 4.539 

2/1/2013 11 :50:00 13.434 4.541 

2/1/2013 11 :51 :00 13.429 4.543 

2/1/2013 11 :52:00 13.428 4.547 

2/1/2013 11 :53:00 13.424 4.552 

2/1/2013 11 :54:00 13.417 4.561 

2/1/2013 11 :55:00 13.413 4.567 

2/1/2013 11 :56:00 13.411 4.57 

2/1/2013 11 :57:00 13.407 4.571 

2/1/2013 12:00:00 13.407 4.571 

2/1/2013 12:01 :00 13.391 4.582 

2/1/2013 12:02:00 13.392 4.587 

2/1/2013 12:03:00 13.401 4.583 

2/1/2013 12:04:00 13.381 4.595 

2/1 /2013 12:05:00 13.387 4.594 

2/1/2013 12:06:00 13.382 4.602 

2/1/2013 12:07:00 13.36 4.615 

2/1/2013 12:08:00 13.365 4.614 

2/1/2013 12:09:00 13.378 4.61 
2/1/2013 12:10:00 13.372 4.615 

2/1/2013 12:11:00 13.384 4.605 

2/1/2013 12:12:00 13.381 4.608 

2/1/2013 12:13:00 13.391 4.6 

2/1/2013 12:14:00 13.394 4.602 

2/1/2013 12:15:00 13.39 4.608 

Average 13.43 4.49 
Test #: 

Date: 

Time: 

Load: 

CPV SENTINEL UNIT 2 

PARTICULATE TEST 

STACK 02. CO2 DATA 

S-2/STK-PM-100-1 

1/30/2013 

9:26 13:34 

103MW 

O2 

Range 20 

Cal Gas 9.98 

Analyzer Zero 0.12 

Analyzer Span 10.10 

Pre-Bias Zero 0.13 

Pre-Bias Span 9.98 

Post-Bias Zero 0.12 

Post-Bias Span 9.96 

Average Bias Zero 0.12 

Average Bias Span 9.97 

Pre-test zero bias 0.1% 

Pre-test span bias -0.6% 

Post-test zero bias 0.0% 

Post-test span bias -0.7% 

Zero Drift 0.0% 

Span Drift -0.1% 

CO2 

10 

4.96 

-0.02 

5.02 

-0.01 

5.05 

0.24 

5.38 

0.12 

5.21 

0.2% 

0.3% 

2.6% 

3.6% 

2.5% 

3.3% 

Test Results (from data logger average) 

Average 13.02 4.66 

Cal Corrected 13.07 4.42 

O2 CO2 

Date Time % % 

1/30/201 3 9:30:00 13.1 04 4.543 

1/30/2013 9:31 :00 13.103 4.544 

1/30/201 3 9:32:00 13.106 4.542 

1/30/2013 9:33:00 13.103 4.544 

1/30/2013 9:34:00 13.082 4.552 

1/30/2013 9:35:00 13.082 4.554 

1/30/2013 9:36:00 13.083 4.552 

1/30/2013 9:37:00 13.08 4.555 

1/30/2013 9:38:00 13.073 4.56 

1/30/2013 9:39:00 13.057 4.568 
1/30/2013 9:40:00 13.061 4.563 

1/30/2013 9:41 :00 13.057 4.566 

1/30/2013 9:42:00 13.057 4.566 

1/30/2013 9:43:00 13.057 4.565 

1/30/2013 9:44:00 13.05 4.571 

1/30/2013 9:45:00 13.054 4.567 

1/30/2013 9:46:00 13.055 4.563 

1/30/2013 9:47 :00 13.048 4.565 

1/30/2013 9:48:00 13.056 4.559 

1/30/2013 9:49:00 13.04 4.565 

1/30/2013 9:50:00 13.052 4.559 

1/30/2013 9:51 :00 13.037 4.566 

1/30/2013 9:52:00 13.037 4.566 

1/30/2013 9:53:00 13.03 4.568 

1/30/2013 9:54:00 13.044 4.565 

1/30/2013 9:55:00 13.044 4.569 

1/30/2013 9:56:00 13.056 4.567 

1/30/2013 9:57:00 13.063 4.571 

1/30/2013 9:58:00 13.079 4.57 

1/30/2013 9:59:00 13.077 4.579 

1/30/2013 10:00:00 13.1 4.575 

1/30/2013 10:01 :00 13.114 4.574 

1/30/2013 10:02:00 13.119 4.577 

1/30/2013 10:03:00 13.126 4.58 

1/30/2013 10:04:00 13.139 4.576 

1/30/2013 10:05:00 13.133 4.578 

1/30/2013 10:06:00 13.127 4.578 

1/30/2013 10:07:00 13.113 4.583 

1/30/2013 10:08:00 13.118 4.576 

1/30/2013 10:09:00 13.086 4.589 

1/30/2013 10:10:00 13.06 4.6 

1/30/2013 10:11:00 13.054 4.6 

1/30/2013 10:12:00 13.051 4.6 

1/30/2013 10:13:00 13.036 4.604 

1/30/2013 10:14:00 13.019 4.606 

1/30/2013 10:15:00 13.04 4.601 

1/30/2013 10:16:00 13.046 4.603 

1/30/2013 10:17:00 13.058 4.612 

1/30/2013 10:18:00 13.097 4.611 

1/30/2013 10:19:00 13.118 4.614 

1/30/2013 10:20:00 13.125 4.626 

1/30/2013 10:21 :00 13.138 4.629 

1/30/2013 10:22:00 13.14 4.636 

1/30/2013 10:23:00 13.143 4.639 

1/30/2013 10:24:00 13.151 4.638 

1/30/2013 10:25:00 13.16 4.637 

1/30/2013 10:26:00 13.175 4.638 

1/30/2013 10:27:00 13.173 4.645 

1/30/2013 10:28:00 13.186 4.643 

1/30/2013 10:29:00 13.192 4.646 

1/30/2013 10:30:00 13.204 4.643 

1/30/2013 10:31 :00 13.204 4.645 

1/30/2013 10:32:00 13.206 4.648 

1/30/2013 10:33:00 13.191 4.658 
1/30/2013 10:34:00 13.191 4.657 

1/30/2013 10:35:00 13.188 4.66 

1/30/2013 10:36:00 13.198 4.655 

1/30/2013 10:56:00 13.099 4.641 

1/30/2013 10:57:00 13.096 4.651 

1/30/2013 10:58:00 13.104 4.65 

1/30/2013 10:59:00 13.092 4.654 

1/30/2013 11 :00:00 13.112 4.644 

1/30/2013 11 :01 :00 13.111 4.644 

1/30/2013 11 :02:00 13.108 4.644 

1/30/2013 11 :03:00 13.088 4.65 

1/30/2013 11 :04:00 13.091 4.646 

1/30/2013 11 :05:00 13.089 4.647 

1/30/2013 11 :06:00 13.081 4.653 

1/30/2013 11 :07:00 13.074 4.655 

1/30/2013 11 :08:00 13.091 4.644 

1/30/2013 11 :09:00 13.089 4.643 

1/30/2013 11 :10:00 13.092 4.643 

1/30/2013 11 :11 :00 13.088 4.646 

1/30/2013 11 :12:00 13.089 4.644 

1/30/2013 11:13:00 13.094 4.641 

1/30/2013 11:14:00 13.106 4.635 

1/30/2013 11:15:00 13.102 4.636 

1/30/2013 11 :16:00 13.093 4.639 

1/30/2013 11 :18:00 13.137 4.642 

1/30/2013 11:19:00 13.094 4.64 

1/30/2013 11 :20:00 13.044 4.666 

1/30/2013 11 :21 :00 13.088 4.642 

1/30/2013 11 :22:00 13.087 4.64 

1/30/2013 11 :23:00 13.088 4.642 

1/30/2013 11 :24:00 13.087 4.65 

1/30/2013 11 :25:00 13.087 4.655 

1/30/2013 11 :26:00 13.098 4.655 

1/30/2013 11 :27:00 13.095 4.662 

1/30/2013 11 :28:00 13.102 4.663 

1/30/2013 11 :29:00 13.11 4.659 

1/30/2013 11 :30:00 13.096 4.664 

1/30/2013 11 :31 :00 13.104 4.657 

1/30/2013 11 :32:00 13.091 4.66 

1/30/2013 11 :33:00 13.087 4.659 

1/30/2013 11 :34:00 13.071 4.667 

1/30/2013 11 :35:00 13.061 4.668 

1/30/2013 11 :36:00 13.052 4.671 

1/30/2013 11 :37:00 13.043 4.67 

1/30/2013 11 :38:00 13.017 4.675 

1/30/2013 11 :39:00 13.013 4.676 

1/30/2013 11 :40:00 13.016 4.665 

1/30/2013 11 :41 :00 13.008 4.676 

1/30/2013 11 :44:00 13.066 4.659 

1/30/2013 11 :45:00 13.063 4.664 

1/30/2013 11 :46:00 13.058 4.666 
1/30/2013 11 :47:00 13.051 4.668 

1/30/2013 11 :48:00 13.061 4.66 

1/30/2013 11 :49:00 13.062 4.661 

1/30/2013 11 :50:00 13.064 4.657 

1/30/2013 11 :51 :00 13.06 4.66 

1/30/2013 11 :52:00 13.058 4.658 

1/30/2013 11 :53:00 13.051 4.656 

1/30/2013 11 :54:00 13.033 4.656 

1/30/2013 11 :55:00 13.012 4.658 

1/30/2013 11 :56:00 12.99 4.667 

1/30/2013 11 :57:00 12.982 4.668 

1/30/2013 11 :58:00 12.979 4.662 

1/30/2013 11 :59:00 12.975 4.661 

1/30/2013 12:00:00 12.956 4.666 

1/30/2013 12:02:00 13.008 4.664 

1/30/2013 12:03:00 12.921 4.67 

1/30/2013 12:04:00 12.915 4.673 

1/30/2013 12:05:00 12.922 4.666 

1/30/2013 12:06:00 12.919 4.666 

1/30/2013 12:07:00 12.909 4.671 

1/30/2013 12:08:00 12.907 4.672 

1/30/2013 12:09:00 12.898 4.679 

1/30/2013 12:10:00 12.905 4.677 

1130/2013 12:11 :00 12.891 4.688 

1/30/2013 12:12:00 12.892 4.687 

1/30/2013 12:13:00 12.897 4.682 

1/30/2013 12:14:00 12.886 4.694 

1/30/2013 12:15:00 12.886 4.691 

1/30/2013 12:16:00 12.881 4.696 

1/30/2013 12:17:00 12.877 4.696 

1/30/2013 12:46:00 12.873 4.706 

1/30/2013 12:47:00 12.905 4.708 

1/30/2013 12:48:00 12.894 4.717 

1/30/2013 12:49:00 12.887 4.726 

1/30/2013 12:50:00 12.891 4.722 

1/30/2013 12:51 :00 12.889 4.725 

1/30/2013 12:52 :00 12.887 4.726 

1/30/2013 12:53:00 12.886 4.729 

1/30/2013 12:54:00 12.889 4.726 

1/30/2013 12:55:00 12.893 4.728 

1/30/2013 12:56:00 12.894 4.728 

1/30/2013 12:57:00 12.891 4.737 

1/30/2013 12:58:00 12.893 4.736 

1/30/2013 12:59:00 12.894 4.74 

1/30/2013 13:00:00 12.892 4.741 

1/30/2013 13:01 :00 12.869 4.744 

1/30/2013 13:02:00 12.867 4.742 

1/30/2013 13:03:00 12.862 4.749 

1/30/2013 13:04:00 12.859 4.751 

1/30/2013 13:05:00 12.865 4.75 

1/30/2013 13:06:00 12.852 4.76 

1/30/2013 13:07:00 12.848 4.764 
1/30/2013 13:08:00 12.858 4.759 

1/30/2013 13:09:00 12.871 4.756 

1/30/2013 13:10:00 12.878 4.755 

1/30/2013 13:11 :00 12.865 4.765 

1/30/2013 13:12:00 12.873 4.763 

1/30/2013 13:13:00 12.879 4.762 

1/30/2013 13:14:00 12.862 4.775 

1/30/2013 13:15:00 12.872 4.772 

1/30/2013 13:16:00 12.881 4.77 

1/30/2013 13:17:00 12.877 4.775 

1/30/2013 13:18:00 12.868 4.782 

1/30/2013 13:19:00 12.868 4.784 

1/30/2013 13:20:00 12.863 4.787 

1/30/2013 13:21 :00 12.871 4.785 

1/30/2013 13:22:00 12.885 4.78 

1/30/2013 13:23:00 12.886 4.776 

1/30/2013 13:24:00 12.882 4.784 

1/30/2013 13:25:00 12.868 4.795 

1/30/2013 13:26:00 12.88 4.789 

1/30/2013 13:29:00 12.915 4.762 

1/30/2013 13:30:00 12.885 4.796 

1/30/2013 13:31 :00 12.886 4.795 

1/30/2013 13:32:00 12.889 4.787 

1/30/2013 13:33:00 12.891 4.789 

1/30/2013 13:34:00 12.886 4.795 

Average 13.02 4.66 
CPV SENTINEL UNIT 2 

PARTICULATE TEST 

STACK O2• CO2 DATA 

Test #: S-2/STK-PM-100-2 

Date: 1/30/2013 

Time: 13:45 17:51 

Load: 100 MW 

O2 CO2 

Range 20 10 

Cal Gas 9.98 4.96 

Analyzer Zero 0.12 -0.02 

Analyzer Span 10.10 5.02 

Pre-Bias Zero 0.12 0.24 

Pre-Bias Span 9.96 5.38 

Post-Bias Zero 0.13 0.1 6 

Post-Bias Span 9.96 5.26 

Average Bias Zero 0.13 0.20 

Average Bias Span 9.96 5.32 

Pre-test zero bias 0.0% 2.6% 

Pre-test span bias -0.7% 3.6% 

Post-test zero bias 0.1% 1.9% 

Post-test span bias -0.7% 2.4% 

Zero Drift 0.0% -0.8% 

Span Drift 0.0% -1.2% 

Test Results (from data logger average) 

Average 13.18 4.67 

Cal Corrected 13.24 4.34 

O2 CO2 

Date Time % % 

1/30/2013 13:48:00 13.322 4.544 

1/30/2013 13:49:00 13.306 4.552 

1/30/2013 13:50:00 13.633 4.355 

1/30/2013 13:51 :00 15.063 3.487 

1/30/2013 13:52:00 15.99 2.948 

1/30/2013 13:53:00 14.969 3.572 

1/30/2013 13:54:00 14.009 4.142 

1/30/201 3 13:55:00 13.798 4.268 

1/30/2013 13:56:00 13.802 4.262 

1/30/2013 13:57:00 13.798 4.269 
1/30/2013 13:58:00 13.794 4.275 

1/30/2013 13:59:00 13.795 4.277 

1/30/2013 14:00:00 13.796 4.275 

1/30/2013 14:01 :00 13.78 4.281 

1/30/2013 14:02:00 13.768 4.284 

1/30/2013 14:03:00 13.753 4.289 

1/30/2013 14:04:00 13.75 4.293 

1/30/2013 14:05:00 13.754 4.287 

1/30/2013 14:06:00 13.755 4.286 

1/30/2013 14:07:00 13.755 4.284 

1/30/2013 14:08:00 13.812 4.247 

1/30/2013 14:09:00 14.618 3.757 

1/30/2013 14:10:00 15.595 3.176 

1/30/2013 14:11 :00 15.515 3.233 

1/30/2013 14:12:00 14.527 3.832 

1/30/2013 14:13:00 13.551 4.417 

1/30/2013 14:14:00 13.312 4.553 

1/3012013 14:15:00 13.31 4.555 

1130/2013 14:16:00 13.328 4.547 

1/30/2013 14:17:00 13.324 4.551 

1/3012013 14:18:00 13.332 4.547 

1/30/2013 14:19:00 13.305 4.567 

1/30/2013 14:20:00 13.324 4.559 

1/3012013 14:21 :00 13.036 4.74 

113012013 14:22:00 12.956 4.79 

1/30/2013 14:23:00 12.955 4.791 

1/3012013 14:24:00 12.95 4.795 

1/30/2013 14:25:00 12.944 4.8 

1/30/2013 14:26:00 12.957 4.795 

1130/2013 14:27:00 12.96 4.797 

113012013 14:28:00 12.961 4.795 

113012013 14:29:00 12.95 4.806 

1130/2013 14:30:00 12.95 4.809 

1/30/2013 14:31 :00 12.958 4.806 

1/3012013 14:32:00 12.96 4.806 

113012013 14:33:00 12.964 4.806 

1/3012013 14:34:00 12.97 4.803 

1/30/2013 14:35:00 12.969 4.805 

1/30/2013 14:36:00 12.984 4.798 

113012013 14:37:00 12.979 4.804 

113012013 14:38:00 12.971 4.81 

1/3012013 14:39:00 12.969 4.813 

113012013 14:40:00 12.98 4.807 

113012013 14:41 :00 12.974 4.812 

1/30/2013 14:42:00 12.973 4.815 

1/30/2013 14:43:00 12.969 4.82 

1/30/2013 14:49:00 13.022 4.797 

1/30/2013 14:50:00 12.985 4.812 

113012013 14:51 :00 12.979 4.819 

1/30/2013 14:52:00 12.981 4.819 

1130/2013 14:53:00 12.981 4.818 

113012013 14:54:00 12.978 4.822 

1/30/2013 14:55:00 12.98 4.822 
1/30/2013 14:56:00 12.989 4.816 

1/30/2013 14:57:00 12.983 4.823 

1/30/2013 14:58:00 12.979 4.823 

1/30/2013 14:59:00 12.982 4.823 

1/30/2013 15:00:00 12.993 4.817 

1/30/2013 15:01 :00 12.994 4.817 

1/30/2013 15:02:00 12.996 4.816 

1/30/2013 15:03:00 12.993 4.819 

1/30/2013 15:04:00 12.996 4.816 

1/30/2013 15:05:00 12.996 4.816 

1/30/2013 15:29:00 12.999 4.818 

1/30/2013 15:30:00 12.985 4.829 

1/30/2013 15:31 :00 12.986 4.832 

1/30/2013 15:32:00 12.986 4.834 

1/30/2013 15:33:00 12.975 4.841 

1/30/2013 15:34:00 12.974 4.845 

1/30/2013 15:35:00 12.983 4.839 

1/30/2013 15:36:00 12.971 4.847 

1/30/2013 15:37:00 12.963 4.855 

1/30/2013 15:38:00 12.973 4.85 

1/30/2013 15:39:00 12.964 4.856 

1/30/2013 15:40:00 12.964 4.857 

1/30/2013 15:41 :00 12.963 4.856 

1/30/2013 15:42:00 12.957 4.862 

1/30/2013 15:43:00 12.954 4.863 

1/30/2013 15:44:00 12.962 4.858 

1/30/2013 15:45:00 12.959 4.861 

1/30/2013 15:46:00 12.962 4.859 

1/30/2013 15:47:00 12.952 4.863 

1/30/2013 15:48:00 12.965 4.855 

1/30/2013 15:49:00 12.957 4.864 

1/30/2013 15:50:00 12.969 4.852 

1/30/2013 15:51 :00 12.958 4.858 

1/30/2013 15:52:00 12.978 4.841 

1/30/2013 15:53:00 12.992 4.834 

1/30/2013 15:54:00 12.98 4.843 

1/30/2013 15:57:00 12.991 4.832 

1/30/2013 15:58:00 12.988 4.834 

1/30/2013 15:59:00 12.976 4.842 

1/30/2013 16:00:00 12.986 4.836 

1/30/2013 16:01 :00 12.996 4.83 

1/30/2013 16:02:00 13.008 4.824 

1/30/2013 16:03:00 13.009 4.82 

1/30/2013 16:04:00 13.007 4.819 

1/30/2013 16:05:00 13.024 4.806 

1/30/2013 16:08:00 13.003 4.813 

1/30/2013 16:09:00 13.001 4.815 

1/30/2013 16:10:00 13.01 4.804 

1/30/2013 16:11:00 13.009 4.806 

1/30/2013 16:12:00 13.009 4.804 

1/30/2013 16:13:00 12.991 4.816 
1/30/2013 16:14:00 13.011 4.801 

1/30/2013 16:15:00 13.011 4.802 

1/30/2013 16:16:00 13.01 4.8 

1/30/2013 16:19:00 13.031 4.783 

1/30/2013 16:20:00 13.041 4.78 

1/30/2013 16:21 :00 13.019 4.787 

1/30/2013 16:22:00 13.017 4.786 

1/30/2013 16:23:00 13.019 4.785 

1/30/2013 16:24:00 13.019 4.782 

1/30/2013 16:25:00 13.019 4.782 

1/30/2013 16:26:00 13.01 4.785 

1/30/2013 16:27:00 13.01 4.784 

1/30/2013 16:28:00 13.018 4.779 

1/30/2013 16:29:00 13.032 4.77 

1/30/2013 16:30:00 13.019 4.775 

1/30/2013 16:41 :00 13.047 4.749 

1/30/2013 16:42:00 13.008 4.765 

1/30/2013 16:43:00 13.009 4.765 

1/30/2013 16:44:00 13.005 4.768 

1/30/2013 16:45:00 12.997 4.772 

1/30/2013 16:46:00 12.986 4.78 

1/30/2013 16:47:00 12.988 4.777 

1/30/2013 16:48:00 13.008 4.764 

1/30/2013 16:49:00 13.007 4.765 

1/30/2013 16:50:00 13.008 4.76 

1/30/2013 16:53:00 13.054 4.737 

1/30/2013 16:54:00 13.031 4.746 

1/30/2013 16:55:00 13.044 4.739 

1/30/2013 16:56:00 13.046 4.736 

1/30/2013 16:57:00 13.054 4.731 

1/30/2013 16:58:00 13.069 4.719 

1/30/2013 16:59:00 13.059 4.722 

1/30/2013 17:00:00 13.058 4.721 

1/30/2013 17:01 :00 13.049 4.729 

1/30/2013 17:02:00 13.037 4.733 

1/30/2013 17:03:00 13.012 4.743 

1/30/2013 17:05:00 13.058 4.732 

1/30/2013 17:06:00 13.011 4.739 

1/30/2013 17:07:00 13.007 4.743 

1/30/2013 17:08:00 13.007 4.742 

1/30/2013 17:09:00 13.001 4.744 

1/30/2013 17:10:00 13.005 4.742 

1/30/2013 17:11 :00 12.998 4.743 

1/30/2013 17:12:00 12.996 4.744 

1/30/2013 17:13:00 12.995 4.742 

1/30/2013 17:14:00 12.998 4.738 

1/30/2013 17:16:00 13.024 4.722 

1/30/2013 17:17:00 13.009 4.731 

1/30/2013 17:18:00 13.006 4.73 
1/30/2013 17:19:00 13.007 4.729 

1/30/2013 17:20:00 13.007 4.726 

1/30/2013 17:21 :00 13.011 4.721 

1/30/2013 17:22:00 13.003 4.727 

1/30/2013 17:23:00 13.008 4.72 

1/30/2013 17:24:00 12.997 4.727 

1/30/2013 17:25:00 13.01 4.717 

1/30/2013 17:26:00 13.011 4.714 

Average 13.18 4.67 
Test #: 

Date: 

Time: 

Load: 

CPV SENTINEL UNIT 2 

PARTICULATE TEST 

STACK O2, CO2 DATA 

S·2ISTK·PM·100·3 

113112013 

8:33 12:39 

100 MW 

O2 

Range 20 

Cal Gas 9.98 

Analyzer Zero 0.11 

Analyzer Span 10.10 

Pre-Bias Zero 0.13 

Pre-Bias Span 10.07 

Post-Bias Zero 0.12 

Post-Bias Span 10.00 

Average Bias Zero 0.12 

Average Bias Span 10.04 

Pre-test zero bias 0.1% 

Pre-test span bias -0.2% 

Post-test zero bias 0.1 % 

Post-test span bias -0.5% 

Zero Drift 0.0% 

Span Drift -0.3% 

CO2 

10 

4.96 

0.06 

5.09 

0.07 

5.09 

0.31 

5.38 

0.19 

5.23 

0.1% 

-0.1% 

2.5% 

2.9% 

2.4% 

3.0% 

Test Results (from data logger average) 

Average 13.11 4.69 

Cal Corrected 13.08 4.42 

O2 CO2 

Date Time % % 

113112013 8:42:00 13.141 4.468 

113112013 8:43:00 13.186 4.47 

113112013 8:44:00 13.183 4.479 

113112013 8:45:00 13.195 4.476 

113112013 8:46:00 13.177 4.488 

113112013 8:47:00 13.18 4.488 

1131 12013 8:48:00 13.191 4.482 

1131 12013 8:49:00 13.187 4.486 

113112013 8:50:00 13.191 4.483 

1131 12013 8:51 :00 13.181 4.489 
1/31 /2013 8:52:00 13.164 4.498 

1/31 /2013 8:53:00 13.161 4.5 

1/31 /2013 8:55:00 13.231 4.494 

1/31 /2013 8:56:00 13.149 4.508 

1/31 /2013 8:57:00 13.14 4.513 

1/31 /2013 8:58:00 13.147 4.51 

1/31 /2013 8:59:00 13.161 4.501 

1/31/2013 9:00:00 13.161 4.503 

1/31 /2013 9:01:00 13.16 4.504 

1/31 /2013 9:02:00 13.15 4.51 

1/31 /2013 9:03:00 13.156 4.508 

1/31 /2013 9:04:00 13.157 4.507 

1/31 /2013 9:06:00 13.213 4.513 

1/31/2013 9:07:00 13.134 4.523 

1/31 /2013 9:08:00 13.132 4.527 

1/31 /2013 9:09:00 13.134 4.527 

1/31/2013 9:10:00 13.135 4.526 

1/31 /2013 9:11 :00 13.133 4.527 

1/31 /2013 9:12:00 13.131 4.533 

1/31/2013 9:13:00 13.114 4.545 

1/31 /2013 9:14:00 13.126 4.542 

1/31 /2013 9:15:00 13.131 4.54 

1/31 /2013 9:17:00 13.249 4.536 

1/31 /2013 9:18:00 13.128 4.548 

1/31/2013 9:19:00 13.108 4.558 

1/31 /2013 9:20:00 13.096 4.569 

1/31 /2013 9:21 :00 13.056 4.591 

1/31 /2013 9:22:00 13.059 4.592 

1/31 /2013 9:23:00 13.056 4.598 

1/31 /2013 9:24:00 13.061 4.594 

1/31/2013 9:25:00 13.061 4.594 

1/31 /2013 9:26:00 13.065 4.595 

1/31 /2013 9:35:00 13.073 4.574 

1/31/2013 9:36:00 13.105 4.576 

1/31 /2013 9:37:00 13.092 4.589 

1/31 /2013 9:38:00 13.094 4.591 

1/31 /2013 9:39:00 13.103 4.592 

1/31 /2013 9:40:00 13.084 4.598 

1/31 /2013 9:41 :00 13.099 4.598 

1/31/2013 9:42:00 13.09 4.602 

1/31 /2013 9:43:00 13.089 4.604 

1/31 /2013 9:44:00 13.084 4.611 

1/31 /2013 9:47:00 13.097 4.615 

1/31 /2013 9:48:00 13.083 4.62 

1/31 /2013 9:49:00 13.082 4.627 

1/31 /2013 9:50:00 13.073 4.634 

1/31 /2013 9:51 :00 13.081 4.635 

1/31 /2013 9:52:00 13.077 4.638 

1/31 /2013 9:53:00 13.058 4.648 
1/31 /2013 9:54:00 13.08 4.64 

1/31 /2013 9:55:00 13.063 4.65 

1/31/2013 9:56:00 13.077 4.646 

1/31 /2013 9:57:00 13.458 4.378 

1/31 /2013 10:00:00 13.064 4.655 

1/31 /2013 10:01 :00 13.055 4.662 

1/31 /2013 10:02:00 13.039 4.672 

1/31 /2013 10:03:00 13.032 4.681 

1/31 /2013 10:04:00 13.027 4.687 

1/31 /2013 10:05:00 13.03 4.688 

1/31 /2013 10:06:00 13.028 4.689 

1/31 /2013 10:07:00 13.032 4.691 

1/31 /2013 10:08:00 13.034 4.691 

1/31 /2013 10:09:00 13.635 4.282 

1/31 /2013 10:12:00 13.05 4.698 

1/31 /2013 10:13:00 13.042 4.704 

1/31 /2013 10:14:00 13.045 4.707 

1/31 /2013 10:15:00 13.056 4.706 

1/31 /2013 10:16:00 13.053 4.71 

1/31 /2013 10:17:00 13.055 4.713 

1/31 /2013 10:18:00 13.057 4.714 

1/31 /2013 10:19:00 13.046 4.721 

1/31 /2013 10:20:00 13.048 4.723 

1/31 /2013 10:30:00 13.053 4.715 

1/31 /2013 10:31 :00 13.078 4.718 

1/31 /2013 10:32:00 13.083 4.724 

1/31 /2013 10:33:00 13.096 4.724 

1/31 /2013 10:34:00 13.107 4.722 

1/31 /2013 10:35:00 13.098 4.732 

1/31 /2013 10:36:00 13.123 4.725 

1/31 /2013 10:37:00 13.117 4.731 

1/31 /2013 10:38:00 13.125 4.73 

1/31 /2013 10:39:00 13.119 4.735 

1/31 /2013 10:40:00 13.124 4.739 

1/31 /2013 10:43:00 13.288 4.722 

1/31 /2013 10:44:00 13.135 4.739 

1/31 /2013 10:45:00 13.141 4.74 

1/31 /2013 10:46:00 13.141 4.742 

1/31 /2013 10:47:00 13.131 4.749 

1/31 /2013 10:48:00 13.138 4.748 

1/31 /2013 10:49:00 13.145 4.746 

1/31 /2013 10:50:00 13.143 4.748 

1/31 /2013 10:51 :00 13.144 4.749 

1/31 /2013 10:52:00 13.134 4.755 

1/31 /2013 10:53:00 13.138 4.757 

1/31 /2013 10:54:00 13.131 4.764 

1/31 /2013 10:55:00 13.131 4.766 

1/31 /2013 10:56:00 13.132 4.764 

1/31 /2013 10:58:00 13.161 4.763 
1/31 /2013 10:59:00 13,138 4,764 

1/31/2013 11 :00:00 13,139 4,762 

1/31 /2013 11 :01 :00 13,131 4.773 

1/31 /2013 11 :02:00 13,134 4.771 

1/31/2013 11 :03:00 13.136 4.77 

1/31 /2013 11 :04:00 13,135 4,77 

1/31/2013 11 :05:00 13.134 4.773 

1/31 /2013 11 :06:00 13,133 4,776 

1/31 /2013 11 :07:00 13.121 4,783 

1/31/2013 11 :08:00 13,1 13 4,791 

1/31/2013 11 :11:00 13.239 4.76 

1/31 /2013 11 :12:00 13.141 4.773 

1/31/2013 11 :13:00 13,139 4.773 

1/31/2013 11 :14:00 13,134 4.777 

1/31/2013 11 :15:00 13.14 4.774 

1/31/2013 11 :16:00 13.133 4,782 

1/31 /2013 11 :17:00 13,146 4.773 

1/31/2013 11:18:00 13,155 4.769 

1/31 /2013 11 :19:00 13,15 4,771 

1/31/2013 11 :20:00 13. 15 4,773 

1/31/2013 11 :34:00 13.114 4.786 

1/31/2013 11 :35:00 13.125 4.782 

1/31 /2013 11 :36:00 13,122 4.782 

1/31/2013 11 :37:00 13,117 4,786 

1/31/2013 11 :38:00 13,121 4.784 

1/31/2013 11 :39:00 13,115 4.789 

1/31 /2013 11 :40:00 13,115 4.791 

1/31 /2013 11 :41 :00 13.128 4,784 

1/31/2013 11 :42:00 13,121 4.788 

1/31 /2013 11 :43:00 13,116 4.79 

1/31 /2013 11 :46:00 13.131 4,78 

1/31 /2013 11 :47:00 13,119 4.794 

1/31/2013 11 :48:00 13.12 4.794 

1/31 /2013 11 :49:00 13.112 4.796 

1/31/2013 11 :50:00 13.108 4,798 

1/31/2013 11 :51 :00 13,107 4.8 

1/31 /2013 11 :52:00 13,094 4.807 

1/31/2013 11 :53:00 13.092 4,809 

1/31/2013 11 :54:00 13.082 4.814 

1/31 /2013 11 :55:00 13.077 4,818 

1/31 /2013 11 :57:00 13,129 4,802 

1/31/2013 11 :58:00 13.083 4,813 

1/31 /2013 11 :59:00 13.069 4.825 

1/31 /2013 12:00:00 13.076 4.82 

1/31 /2013 12:01 :00 13.058 4.828 

1/31 /2013 12:02:00 13.069 4,822 

1/31/2013 12:03:00 13.051 4,831 

1/31 /2013 12:04:00 13,056 4.828 

1/31/2013 12:05:00 13.056 4.829 

1/31 /2013 12:06:00 13,058 4,824 
1/31/2013 12:10:00 13.107 4.798 

1/31 /2013 12:11 :00 13.094 4.806 

1/31/2013 12:12:00 13.103 4.802 

1/31 /2013 12:13:00 13.104 4.804 

1/31 /2013 12:14:00 13.105 4.804 

1/31 /2013 12:15:00 13.103 4.806 

1/31 /2013 12:16:00 13.106 4.804 

1/31/2013 12:17:00 13.1 4.807 

1/31 /2013 12:18:00 13.104 4.807 

1/31 /2013 12:28:00 13.032 4.822 

1/31 /2013 12:29:00 13.047 4.826 

1/31/2013 12:30:00 13.056 4.826 

1/31 /2013 12:31 :00 13.056 4.828 

1/31 /2013 12:32:00 13.057 4.827 

1/31 /2013 12:33:00 13.058 4.828 

1/31 /2013 12:34:00 13.05 4.832 

1/31 /2013 12:35:00 13.062 4.826 

1/31 /2013 12:36:00 13.064 4.826 

1/31 /2013 12:37:00 13.07 4.824 

1/31 /2013 12:38:00 13.074 4.823 

1/31 /2013 12:39:00 13.069 4.826 

Average 13.11 4.69 
APPENDIX D GENERAL EMISSIONS CALCULATIONS 

R0410673 D-1 .. Delta __ ...... -/'). 
GENERAL EMISSION CALCULATIONS 

1) Stack Gas Velocity 

2) 

A. Stack gas molecular weight, Ib/lb-mole 

MWdry = 0.44 * %C02 + 0.32 * %02 + 0.28 * %N2 

MWwet = MWdry * (1- Bwo ) + 18 * Bwo 

B. Absolute stack pressure, iwg 

Ps = Pbar + Psg 

13.6 

c. Stack gas velocity, ftlsec 

Vs = 2.9 * Cp * -J IlP * Fs * 

Moisture 

A. Sample gas volume, dscf 

Vmstd = 0.03342 * Vm * (Pbar + 

B. Water vapor volume, scf 

v = 0.0472 * V * Tref 

wstd Ie 528 oR 

29.92 * 28.95 

P, * MWwet 

IlH ) * Tref * Yd 13.6 Tm 

c. Moisture content, dimensionless 

Bwo = 

3) Stack gas volumetric flow rate 

A. Actual stack gas volumetric flow rate, wacfm 

Q = v * A * 60 s s 

B. Standard stack gas flow rate, dscfm 

R0410673 D-2 De/lat6. "" ....... "",,.,-
Q 

sd 

= Q * (1-B wo ) * T

Ts 

ref ~ 29.92 

4) Gaseous Mass Emission Rates, Ib/hr 

M = ppm * MWj * Q Sd * 60 

SV * 106 

5) Emission Rates, Ib/MMBtu 

Ib ppm*MW; *F * 20.9 

MMBtu SV*106 20.9 - %0, 

6) Emission Factor, Ib/MMSCF 

:-:-::-:-=1 b---:-= = I b * H HV 

MMSCF MMBtu 

VI . Percent Iso kinetic 

17.32 x T, Wm sId) 528 0 R 

1 = , x --- (1- Bwa)O x V, x Ps x Dn T"f 

VII . Particulate emissions 

a) Grain loading, gr/dscf 

C = 0.01543 (MnN m SId) 

b) Grain loading at 12% CO" gr/dscf 

Cm• co, = C (12/% CO,) 

c) Grain loading at 3% 0 " gr/dscf 

C3%02 = C * 17 .9/(20.9-%0,) 

d) Mass emissions, Ib/hr 

M = C x Qsd x (60 min/hr)/(7000 gr/lb) 

e) Particulate emission factor 

6 llb 20 .. 9 lb l lO Btu = ex x F x---- 7000gr 20.9 - % 0 , 

R0410673 D-3 
Nomenclature: 

As 

Bwo 

C12%C02 

C3%02 

C 

Cp 

On 

F 

H 

HHV 

I 

Mn 

M; 

MW 

Mwi 

o 

P 

Pbar 

Ps 

P Sg 

Q 

Q ws 

QSd 

SV 

Tm 

Tref 

Ts 

Vs 

V'c 

Vm 

Vmstd 

VwStd 

Yd 

R0410673 

= stack area, ft2 

= flue gas moisture content, dimensionless 

= particulate grain loading, gr/dscf corrected to 12% CO2 

= particulate grain loading, gr/dscf corrected to 3% CO2 

= particulate grain loading, gr/dscf 

= pitot calibration factor, dimensionless 

= nozzle diameter, in. 

= fuel F-Factor, dscf/MMBtu @ 0% O2 

= orifice differential pressure, iwg 

= fuel higher heating value, Btu/SCF 

= % isokinetics 

= mass of collected particulate, mg 

= mass emission rate of specie i, Ib/hr 

= molecular weight of flue gas, Ib/lb-mole 

= molecular weight of specie i: 

S02: 64 

NO,: 46 

CO: 28 

HC: 16 

= sample time, min. 

= average velocity head, iwg = -J ~P)2 

= barometric pressure, inches Hg 

= stack absolute pressure, inches Hg 

= stack static pressure, iwb 

= wet stack flow rate at actual conditions, wacfm 

= wet stack flow at standard conditions, wscfm 

= dry standard stack flow rate, dscfm 

= s~ecific molar volume of an ideal gas at standard conditions , 

ft lib-mole 

= meter temperature, oR 

= reference temperature , OR 

= stack temperature, OR 

= stack gas velocity, fUsec 

= volume of liquid collected in impingers, ml 

= uncorrected dry meter volume, dcf 

= dry meter volume at standard conditions, dscf 

= volume of water vapor at standard conditions, scf 

= meter calibration coefficient 

D-4 Della/:" ................ ,.....-.. 
APPENDIX E CHAIN OF CUSTODY 

R0410673 E-1 De/laIJ. ,,-....... ~, ... --' 
CHAIN OF CUSTODY 

CLIENT: Sentinel ~ TEST DATE(S): 1130/2013 211/2013 

LOCATION: 2 SAMPLER(S): SS 

SAMPLE LOCATION: Stk PROJECT MANAGER: BF 

TEST METHOD(S): SCAQMDS.1 DATE DUE: 219/2013 

OUTSIDE LAB REQUIRED?: No COMPLIANCE TEST? Yes 

.t 0 

1130/2013 S2ISjk·PM·100·1 SCAQMD5.1 Probe Une Imp. 1 SS Water 

113012013 S2fStk·PM·1 00-' SCAQMD 5.1 5.1 Filter 1 SS 55mm 

1/30/2013 S2IStk·PM·100·2 SCAQMO 5.1 Probe Line 1m . 1 SS Water 

1/30/2013 S2IStk·PM-100·2 SCAQMD S.1 5.1 Filter 1 SS 55mm 

113112013 S2IStk·PM·100·3 SCAQMD S.1 Probe, Line, 1m . 1 SS Water 

1131/2013 S2lStk-PM-100-3 SCAQMD 5.1 5.1 Filter 1 SS 55mm 

211/2013 S2IStk·PM·7S·1 SCAQMD S.1 Probe. Line, Imp. 1 SS Water 

21112013 S2IStk·PM·7S·1 SCAQMDS.1 5.1 Filter 1 SS 55mm 

21112013 S2IStk·PM·SO·1 SCAQMD S.1 Probe Line Imp. 1 SS Water 

211/2013 S2IStk-PM-50-1 SCAQMDS.1 5.1 Filter 1 SS 55mm 

21112013 S2IStk·PM·-FB SCAQMDS.1 Probe, Line. Imp. 1 SS Water 

211/2013 S2IStk·PM FB SCAQMDS.1 5.1 Filter 1 SS 5Smm 

211/2013 S2IStk·PM·-RB SCAQMDS.1 Blank 1 SS Waler 

~tal ~ampJes 3 

Rea entl water I I ea ent ot s: S I 

I 

/?~j ' Z?d ~~~~~ 

I I 

Di7TI~~ '4 _ .,.....~ )7/ b 0 I~t:#p ~~ - IvY/emt; 

!!. 
CLIENT; 

LOCATION; 

SAMPLE LOCATION; 

TEST METHOD(S); 

OUTSIDE LAB REQUIRED?; 

71"i2oT'3 

'30/2013 

'3Oi2013 

21172'013 

1/201 

Sentinel ~~ 

2 

SII< 

SCAQMD 207.1 

No 

TIME T TEST# 

i2lStk·NH3-·FB Blank 

S2ISII<-NH3-100-1 

S2JStk-NH3·100-2 

_S~Stk-NH~-?5-1 

- ,- -

S2IStk·NH3·50-2 

S2IStk-NH3- RB Blank 

S2IStk-NH3---RB Blank 

'-______ ...;R..:;e"'ag"e"'n':..;L"'o':.:#':.,:s"' I_ . _ _ ________ _ 

CHAIN OF CUSTODY 

TEST DATE(S); 1130/2013 2/112013 

SAMPLER(S); SS 

PROJECT MANAGER; BF 

DATE DUE; 219/2013 

COMPLIANCE TEST? Yes 

Method SAMPLE I 

SCAQMD 207.1 Probe, lir 

SCAQMD 207.1 Probe line , 

SCAQMD 207.1 Probe nne 

SCAQMD 207.1 Probe line 

be line IrTiPIi1gers 1 SS 0.1 N H2SO4 

be, line . 1m 'n ers 1 SS 0.1 N H2SC 

SCAQMD 207.1 Probe line 1m In ers 1 SS 0.1 N HZSC 

SCAQMD 207.1 3110020/V9 1 SS 0.1 N H2SC 

5CAQMD 207.1 3110020/Vl0 1 55 0.1 N H2SC 

9 

J A-t /1 A/I ~EA15DBY /. _ d ___ DA;"ry~,.., EiiJ:f~!?! 6z'tbEITi'1&n 

I • 1 ,,= 1 1--" r- .. 1 -, (I -~ 

~ 
A~!P /301z..~ 

CHAIN OF CUSTODV 

CLIENT: Sentinel CQ.owt TEST DATE(S): 1130/2013 21112013 

LOCATION: 2 SAMPLER(S): .:.:R"'M ___________ _ 

SAMPLE LOCATION: SII< PROJECT MANAGER: 

TEST METHOD(S): SCAQMD 25.3 DATE DUE: 

OUTSIDE LAB REQUIRED?' Yes 

C7t7 1/30/2013 S2I 1I<.,g ·1()()'1A _§C 2(,.. v.' '' .~" 07" 1130/2013 S2ISIk·VOC-1()().1B SCAQMD 25.3 Canisterj 

IJ 7'f f 211 /2013 S2ISII<·VOC-50·1A SCAQMD 25.3 Canisterj 

..1! 

COMPLIANCE TEST? 

tJIII[ 

-srr 

0() 211 /2013 S2ISII<.VOC-50·1B SCAQMD 25.3 Canlsterl O!.../ 211 /2013 S2ISII<·VOC-75-1A SCAQMD25.3 Canl __ --;::;;:O, , .. ' "0- ~ 21112013 S2ISIk·VOC.75-1B SCAQMD25.3 Csni __ .r~ 1 RM 

.o1PJ 

6 

~"'iiit Reagent L({ 's: , ' --

...l 

BF 

21912013 

Ves 

v 

~ ~ 

l,zzj~)3 ~;@ I I 2S!:i:'i jif I Olii 6 ~'" Note: Can~t.r #00<>403 and toQO.411 were voided ...... Plea .. do not analyze. ' .. 

-MFA 
APPENDIX F INSTRUMENT STRIP CHARTS 

R0410673 F-1 

Delfal1 ",o-.'-H,_" 





















APPENDIX G FACILITY PERMIT TO OPERATE CONDITION 029.1 

R0410673 G-1 .. 

De/ta """,~ ........... -~ .... 
SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 Copley Drtve, Diamond Bar, CA 91765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

Section H Page: 35 

Facility 10: 152707 

R~inon#: 0 

Date: April IS. 2011 

SECTION H; PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with the terms and conditions set forth below: 

The operator shall also install and maintain a device to continuously record the 

parameter being measured 

The measuring device or gauge shall be accurate to within plus or minus 5 

percent. It shall be calibrated once every twelve months 

It shall be calibrated once every twelve months 

The pressure drop across the catalyst shall not exceed 12 inches water column 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(aXI)-BACT, 12-6-2002; RULE 

1703(aX2) - PSD-BACT, 10-7-1988; RULE 2005, 5-6-2005) 

[Devices subject to this condition: C4, CIO, C16, C22, C28, C34, C40, C46) 

D 12.5 The operator shall install and maintain a(n) non-resettable elapsed time meter to 

accurately indicate the elapsed operating time from the engine. 

[RULE J 110.2,2-1-2008; RULE 1303(b)(2)-OlTset, 5-10-1996; RULE 1303(b)(2) 

-Offset, 12-6-2002; RULE 1470, 6-1-2007; RULE 2012, 5-6-2005) 

[Devices subject to this condition: D49) 

D29.1 The operator shall conduct source testes) for the pollutant(s) identified below. 

Pollutant(s) to Required Test Method(s) Averaging Time I Test Location 

be tested 

NOX emissions District method 100.1 I hour Outlet of the SCR 

serving this equipment 

CO emissions District method 100.1 I hour I Outlet of the SCR 

serving this equipment 

SOX emissions I AQMD Laboratory 

Method 307-9\ 

Not Applicable I Fuel sample 

VOC emissions I District Method 25.3 I hour I Outlet of the SCR 

serving this equipment 
SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 Copley Drive, Diamond Bar, CA 91765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

Section H Page: 36 

Facilitv 10: 152707 

Revision #: 0 

Date: April 15, 20J 1 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with the terms and conditions set forth below: 

PM 10 

emissions 

NH3 emissions 

I District Method 5 

I District method 207.1 

and 5.3 or EPA method 

17 

4 hours 

1 hour 

I Outlet of the SCR 

serving this equipment I Outlet of the SCR 

serving this equipment 
~-

SOUTH COAST AIR QUALITY MANAGE.MENT DISTRICT 

21865 Copley Drive, Diamond Bar, CA 91765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

Section H 

Facility lD: 

Revision II: 

Date: 

Page: 37 

152707 

o 

April IS. 20)1 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with the terms and conditions set forth below: 

The test shall be conducted after AQMD approval of the source test protocol, but 

no later the later of 180 days after initial start-up or three hundred hours of 

operations after start-up. The AQMD shall be notified of the date and time of the 

test at least 10 days prior to the test 

The test shall be conducted to determine the oxygen levels in the exhaust. In 

addition, the tests shall measure the fuel flow rate (CFH), the flue gas flow rate, 

and the turbine generating output in MW. 

The test shall be conducted in accordance with AQMD approved test protocol. 

The protocol shall be submitted to the AQMD engineer no later than 45 days 

before the proposed test date and shall be approved by the AQMD before the test 

commences. 

The test protocol shall include the proposed operating conditions of the turbine 

during the tests, the identity of the testing lab, a statement from the testing lab 

certifying that it meets the criteria of Rule 304, and a description of all sampling 

and analytical procedures 

The test shall be conducted when this equipment is operating at maximum, 

average, and minimum loads_ 

For natural gas fired turbines only, VOC compliance shall be demonstrated as 

follows: a) Stack gas samples are extracted into 

final canister pressure between 400-500 mm Hg 

canisters are done with zero gas analyzed/certified 

total hydrocarbon as carbon, and c) Analysis of 

TO-l2 (with pre concentration) and temperature 

samples for analysis is not below 70 deg F. 

Summa canisters maintaining a 

absolute, b) Pressurization of 

to contain less than 0.05 ppmv 

canisters are per EPA Method 

of canisters when extracting 

The test shall be conducted for compliance verification of the BACT VOC 2.0 

ppmv limit. 

The test results shall be reported with two significant digits. 
SOUTH COAST AIR QUALllY MANAGEMENT DISTRICT 

21865 Copley DrIve, DIamond Bar, CA 91765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

Section H 

Facility ID: 

Revision Ii: 

Date: 

Page: 38 

152707 

o 

April 15, 201 1 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with tbe terms and conditions set forth below: 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(aXl)-BACT, 12-6-2002; RULE 

1303(b)(2)-Offset, 5-10-1996; RULE 1303(b)(2)-Offset, 12-6-2002; RULE 1703(a)(2) -

PSD-BACT, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: DI, D7, 013, D19, D25, D31, 037, D43] 

D29.2 The operator shall conduct source testes) for the pollutant(s) identified below. 

Pollutant(s) to 

be tested 

NH3 emissions 

I Required Test Metbod(s) 

District method 207.1 

and 5.3 or EPA method 

17 

Averaging Time 

I hour 

I Test Location 

I Outlet of the SCR 

serving this equipment 

The test shall be conducted and the results submitted to the District within 45 

days after the test date. The AQMD shalI be notified of the date and time of the 

test at least 7 days prior to the test. 

The test shall be conducted at least quarterly during the first twelve months of 

operation and at least annually thereafter. The NOx concentration, as detennined 

by the CEMS, shall be simultaneously recorded during the ammonia slip test. If 

the CEMS is inoperable, a test shall be conducted to determine the NOx 

emissions using District Method 100.1 measured oyer a 60 minute averaging time 

period. 

If the turbine is not in operation during one quarter, then no testing IS required 

during that quarter 

The test shall be conducted to demonstrate compliance with the Rule 1303 BACT 

concentration limit 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(a)(I)-BACT, 12-6-2002] 

[Devices subject to this condition: Dl, D7, 013, D19, D25, D31, D37, D43] 
APPENDIX H CORRESPONDENCE AND TEST PLAN 

R0410673 H-1 "' Delta ............... _ ~ .. 
Bob: 

Here is an answer to one of the issues for the CPY Sentinel testing. 

From: Carey Willoughby [mailto:CWilloughby@aqmd.gov] 

Sent: Wednesday, January 09, 2013 10:09 AM 

To: Tom W. Andrews 

Subject: RE: epy Sentinel voe Tests 

Mr. Andrews, 

Simultaneous duplicate sampling (six canister samples vs. nine sample canisters) for VOC is 

acceptable to the SCAQMD. 

Sincerely, 

Carey "'Wi{{oUEJfijjy 

Air Quaaty 'E11fJineer II 

SC.JI.Q:.M'D 

21865 Coyfey 'Drive 

'Diamoruf'.Bar, CA 91765 

'l'ef (909) 396-3006 

:fax: (909) 396-2099 

cwiC{OUOfi6y@aqmd:.IJOV 

From: Tom W. Andrews [mailto:TAndrews@sierraresearch.com] 

Sent: Wednesday, January 09, 2013 9:39 AM 

To: Carey Willoughby 

Cc: W. Andrews, Tom 

Subject: CPV Sentinel voe Tests 

Carey: 

Per our telecon this morning, for the VOC tests the test team would like to take duplicate 

simultaneous samples rather than triplicate samples in series at each of the three gas turbine 

loads. In other words a total of six canister samples vs. nine canister samples. Could you please 

confirm this is acceptable to the SCAQMD. Thanks. 

Tom Andrews 

1801 J Street 

Sacramento, CA 95811 

(916) 273-5139 (direct/voice) 

(916) 444-8373 ifax) 
SOURCE TEST PROTOCOL FOR INITIAL 

COMPLIANCE TESTING AT CPV SENTINEL ENERGY 

PROJECT UNITS 1 - 8 

PREPARED FOR: 

GEMMA POWER SYSTEMS CALIFORNIA, INC. 

2461 MAIN STREET 

GLASTONBURY, CONNECTICUT 06033 

FOR SUBMITIAL TO: 

SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 COPLEY DRIVE 

DIAMOND BAR, CALIFORNIA 91765-4178 

PREPARED BY: 

DELTA AIR QUALITY SERVICES, INC. 

1845 N. CASE ST. 

ORANGE, CALIFORNIA 92865 

714-279-6777 

ROBERT A. FINKEN 

DECEMBER 7,2012 

DOCUMENT NUMBER: R0210458·R1 

Air 

8ellll~ Quality Services, Incorporated 
CONFIDENTIALITY STATEMENT 

This information contained in this communication is intended exclusively 

for the individual or entity to which it is addressed. This communication may 

contain information that is proprietary, privileged or confidential or otherwise 

legally exempt from disclosure. If you are not the named addressee, you are not 

authorized to read, print, retain, copy, or disseminate this message or any part of 

it. 

R0210458-R1 ii 1Je1/a/j. 

.. --
CONTENTS 

SECTION 

1,0 INTRODUCTION "'" ",.", ""'" "" "" " "'" "'" """ ""'''' " " " .... "" .. ," """,, .. '" ,,", " ... ""." 1 

2.0 UNIT DESCRIPTION AND TEST CONDITIONS """'''''''''' '''''' ''''' '' '''' ' ''''''''''' '' ''''''' 2 

2,1 UNIT DESCRIPTION""" " .. , """ "",,,,,,, '"''''',''' ".,,' ...... """.", .. , '" ",," '" ,,, .. ,'''''' 2 

2,2 TEST CONDITIONS "". "." ", '" ",,,, .. ,,, .. ,,, ",, ' "", .. , '" " .... " .... "" .. '" .. "" ... " " .. " " " 4 

2,3 SAMPLE LOCATION" """, ... " " .. " " .. ' " ." " .. ,' "" " .. '" " .. ,,"" .. ,,, .. , "" .,,'" ",", ... , " " 5 

3,0 TEST DESCRIPTION"." ""'" '' ''' ''''' ","',," " .. ' " .""."' .. " "" .. " " ... '" " .. "' ... " " .. ,,' .. " "" 7 

3,1 O2• CO2• NOx AND CO """""""".".""" .. "."" .. ""."",,.""" .. ",,",," .. ,,.,,",,"""" 8 

3,2 NH3 BY SCAQMD METHOD 207,1 "".""""""."."""" .. """"".".".".""" .. """." 9 

3,3 SOx BY SCAQMD METHOD 307,91 ".""""""""".".,,".""" .. "" .. " " .. ,,.,, .. """'" 9 

3.4 ROG BY MODIFIED SCAQMD METHOD 25.3""."""" .. ,,,,,,,,,.,,.,,,, .. ,,.,, .. ,,,,,,,,, 9 

3.5 PM BY SCAQMD METHOD 5,1 """""'"''''''''''' '''' '' '''''' ''''''' '' ''''' '''' '''''''''''' ''''' 13 

4,0 REPORTING """ .... ,' , .. ",," ,"' .. .. '" .... " ... ".", ,,"" ",, ' "'" " .. " , ' .. "" " .. ,,' ... " " ... " , ... "' ''' 15 

APPENDICES 

A QUALITY ASSURANCE" "",," ... ". ," "" ... , ". ''''' ,''',' " .. " ".". ", ... ,," ", .. , .. "" ... "",'" "A-1 

B TEST METHODS , "''' ' '' .. '' " " ... ,' .. "" .. , ", .... , .. ,," ". '" ".,," ".".'" .. ,,''' .. '' ""',' " ... "".,," B-1 

C CALCULATIONS, '" "."".""".,,".,, "' .,, '" ." " ... " .. ' " .. ' "'" " ..... ""."'" .. "" .. "" .... "'"'' C-1 

o FORMS " ' ''' ' ' """ . '" ". "" "" "'" ". """."."." """" """ '"'''' ""'" "" .. "" ... " .... "" "."."., 0 -1 

E FACILITY PERMIT TO OPERATE CONDITION 029,1 """ .... " ... """"" ..... ""."",,.E-1 

R021 0458-R 1 iii llella/}. "'''-'--
1.0 INTRODUCTION 

Delta Air Quality Services, Inc. has been contracted by Gemma Power Systems 

California. Inc. (GEMMA) to perform the initial Permit to Operate Compliance Testing at 

the CPV Sentinel Energy Project Units 1, 2, 3, 4, 5, 6, 7, and 8. Condition D29.1 of the 

Permit to Operate requires source tests within 180 days of initial startup. This document 

will serve as the test plan for the aforementioned tests. 

Tests will be performed at three load conditions to determine oxides of nitrogen 

(NOx), carbon monoxide (CO), oxides of sulfur (SOx), reactive organic gases (ROG's), 

particulate matter (PM), and ammonia (NH3) emissions. 

Bob Finken will be the Senior Program Manager for Delta and can be reached at 

(714) 279-6777. No conflict of interest, as defined in SCAQMD Rule 304, exists between 

Gemma or CPV Sentinel Energy Project and Delta. 

Section 2.0 of this document provides a description of the facilities and sample 

locations. A description of the sampling strategy and test methods is provided in Section 

3.0. Section 4.0 outlines the final source test report format. A more detailed description 

of the test methods, calculations, and quality assurance procedures is provided in the 

Appendices. 

R021 0458-R 1 1 .. /le/tat1 _ ....... -
2.0 UNIT DESCRIPTION AND TEST CONDITIONS 

2.1 UNIT DESCRIPTION 

CPV Sentinel Energy Project is located at 62575 Powerline Road, Desert Hot 

Springs, California 92240. The facility consists of eight (8) identical generating units. 

The CPV Sentinel Energy Project consists of eight (8) LMS100PA combustion 

turbines in simple cycle operation. The units are natural gas fired with a rated heat input 

of 891 .7 MMBtu per hour at 72 degrees Fahrenheit. Each LMS100PA employs water 

injection and is equipped with a CO catalyst and Selective Catalytic Reduction (SCR) 

system for NOx control. 

The LMS100PA is a General Electric (GE) combustion turbine with an intercooler 

located between the low pressure compressor (LPC) and high pressure compressor 

(HPC). Off engine combustion air to closed loop water intercooling is used for increased 

gas turbine thermal efficiency. Heat removed from the off-engine intercooler is circulated 

through a closed loop cooling system. Heat is rejected from the closed loop cooling 

system to an open loop cooling system via plate and frame heat exchangers. The open 

loop system rejects heat via a mechanical draft counterflow cooling tower. The cooling 

tower is provided with drift elimination to comply with air emissions limits. 

Figure 2-1 presents a block diagram of the units. Figure 2-2 shows a general 

arrangement of the major components. 

R021045B-R1 2 DeIIai1 

... _--
FIGURE 2-1 

SIMPLIFIED PROCESS BLOCK DIAGRAM 

CPV SENTINEL ENERGY PROJECT COMBUSTION TURBINES 

Simplified Process Flow Diagram 

Air 

Water 

Cooling Tower 

Air 

Water 

Heat 

Closed Loop Exhaust to Atm. 

Cooling 

Air LMS100PA Exhaust CO Catalyst SCR IWater Ammonia 

Natural Gas Fuel Demineralized 19% Aqueous 

R021 0458-R 1 Oe/lIl1 

........ ...--- 3 
FIGURE 2-2 

GENERAL ARRANGEMENT OF MAJOR COMPONENTS 

;.u.o. .r ... ':rD-".- Y' .... .r.AoItII 

-. .. ....... .. .. ..... ..... _ ... .... ........ .lk9++=d._ ............. .. .. . 

A \ wr· ' 

• "'f t''''T·-4. B.UT .... ;. t .. ~,.. 

(...,.. 

2.2 TEST CONDITIONS 

The permit requires that the tests will be performed at three operating conditions; 

1) maximum, 2) average, and 3) minimum load. Full load is nominally 100 megawatts 

and minimum load will be approximately 50 megawatts. Since these will be the initial 

tests for the units and no long term average will have been established, average 

conditions will be approximated at 75% of capacity or approximately 75 megawatts. 

R021 0458·R 1 4 
Unit operating data will be gathered during the tests by the facility from the CEMS 

DAS. These data will include, at a minimum: 

• Fuel flow rate 

• Turbine generating output (MW) 

• Ammonia Flow 

• Exhaust Temperatures 

• Exhaust Flow Rates 

2.3 SAMPLE LOCATION 

There are four 6" test ports located at 90 degrees apart around the circumference 

of the 13'6" diameter stacks. The ports are located 323" downstream (2.0 diameters) of 

the nearest flow disturbance (duct breeching) 84" upstream (0.5 diameters) of the 

nearest flow disturbance (silencers). The sampling location meets the minimum 

requirements of SCAQMD Method 2.1, being >2 diameters downstream and >0.5 

diameters upstream of the nearest flow disturbances. Figure 2-3 presents the details of 

the sample location. 

FIGURE 2-3 

SAMPLE LOCATION DETAILS 

Inside Diameter, in. 

- 162 4--

Stack Exit 1080.0 in. 

Silencer Bottom 925.9 in. 

Ports 841 .6 in. 

Platform 789.6 in. 

Base 01 Slack 518.5 in. 

Grade 0.0 in. 

R021 0458-R 1 

T 

84 Distance A, inches, 0.5 Diameters 

! Sample ports 

T 

323 Distance Bt inches, 2.0 Diameters 

+_...;E::;x:;::hauSI Flow 4 

Elevation View 

5 

90 ft. 

66 II. 

o fl. 

Delta,1. 

--.--
Sample 

Point 

2 

3 

4 

5 

6 

7 

8 

9 

10 

11 

Prior to performing the tests, gaseous stratification will be investigated with a 12 

point traverse as described in 40 CFR 75, and the presence of cyclonic flow will be 

checked using the techniques described in SCAQMD Method 2. 

If stratification is less than 10% or less than 1 ppm, all future gaseous 

concentration measurements will be made from a single point. If stratification is greater 

than 10% and greater than 1 ppm, all future concentration measurements will be 

performed using a multi-point traverse (3-point short line, 3-point long line, or 12-points 

(using 40 CFR Part 75 criteria)). 

A 16-point cyclonic flow traverse will be performed with an S-type pitot tube. If 

the average yaw angle is less than 10 degrees, the location will be deemed acceptable 

for Method 2.1 velocity measurements. 

Table 2-1 illustrates the location of sample traverse pOints. 

TABLE 2-1 

SAMPLE POINT LAYOUT 

PM (24 pts.) Flow Disturbance (16 pts.) Strat.lNH3 (12 Pts.) 3 pI. Long Line CEMS 3 pI. Short Line CEMS 

% of in. % of In. % of in. % of in. % of 

Diameter from Wall Diameter from Wall Diameter from Wall Diameter from Wall Diameter 

2.1 3.4 3.2 5.2 4.4 7.1 16.7 27.1 N/A 

6.7 10.9 10.5 17.0 14.6 23.7 50 81.0 N/A 

11 .8 19.1 19.4 31.4 29.6 48.0 

17.7 28.7 32.3 52.3 

25 40.5 67.7 109.7 

35.6 57.7 80.6 130.6 

64.4 104.3 89.5 145.0 

75 121 .5 

82.3 133.3 

86.4 140.0 

93.3 151.1 

Prior to performing the tests, gaseous stratification will be investigated with a 12 

point traverse as described in 40 CFR 75, and the presence of cyclonic flow will be 

checked using the techniques described in SCAQMD Method 2.1. 

If stratification is less than 10% or less than 1 ppm, all future gaseous 

concentration measurements will be made from a single point. If stratification is greater 

than 10% and greater than 1 ppm, all future concentration measurements will be 

performed using a multi-point traverse (3-point short line, 3-point long line, or 12-points 

(using 40 CFR Part 75 criteria» . 

A 16-point cyclonic flow traverse will be performed with an S-type pitot tube. If 

the average yaw angle is less than 10 degrees, the location will be deemed acceptable 

for Method 2.1 velocity measurements. 

R0210458-R1 6 llella;}. "' ...... _-

in. 

from Wall 

15.7 

47.2 
3.0 TEST DESCRIPTION 

Table 3-1 summarizes the test methods and techniques which will be used as the 

reference methods. The test matrix has been developed to meet the requirements of 

Section 29.1 of the facility Permit (Application Number 472137) dated April 15, 2011 . 

The permitted emission limits are summarized in Table 3-2. The following 

sections describe each method in further detail. Flue gas Oxygen and Carbon Dioxide 

concentration will be measured in conjunction with all tests using SCAQMD Method 

100.1 . The flue gas flow rate will be measured in conjunction with each particulate test. 

This measured flue gas flow rate in each duct will be used for all emission rate 

calculations of NOx, CO, NH3, ROG's and SOx. 

TABLE 3-1 

TEST MATRIX 

Parameter Method 50% Load 75% Load 100% Load Test Duration 

NOx SCAQMD 100.1 1 run 1 run 1 run 60 minutes 

02/C02 SCAQMD 100.1 With each run 

CO SCAQMD 100.1 1 run 1 run 1 run 60 minutes 

NH3 SCAQMD 207.1 2 runs 2 runs 2 runs 60 minutes 

S02 SCAQMD 307.91 2 samples N/A 

PM EPA 201NSCAQMD 5.1 1 run 1 run 1 run 240 minutes 

ROG Modified SCAQMD 25.3 3 runs 3 runs 3 runs - 60 minutes(1) 

1) ROG tests will be nominally 60 minutes. Flow controllers will be setup for 60 minutes. The test will be 

performed unlil the canister vacuum reaches approximately 10 "Hg. Actual test time may be less than or 

more than 60 minutes per sample. 

R 021 0458-R 1 7 De/Ia/'). 

»--="' 
TABLE 3-2 

CPV SENTINEL ENERGY PROJECT 

PERMIITED EMISSION LIMITS 

Parameter Units 

ppm@15%02 

ppm @ 15% O2 

Ibs/MMscf 

co ppm @15%02 

NHa ppm@ 15% O2 

gr/dscf @ 3% O2 

Particulate gr/dscf @ 12% CO2 

Ib/hr 

Ibs/MMscf 

(Ib/hr equivalent) 

Ib/MMBtu 

Ibs/MMscf SOx 

ROG's ppm@ 15% O2 

(1) The 12.26 IbslMMscf is a RECLAIM emission factor, not a limij. 

(2) This is stated in the permit as an emission factor. 

3.1 O2• CO2• NOx AND CO 

Limit 

2.5 

15 

12.26(1) 

4 

5 

0.Q1 

0.1 

11 

5.71(2) 

(5.0) 

0.06 

0.69 

2.0 

Rule 

1703(a)(2) 

40 CFR 60 

2012 

1703(a)(2) 

1303(a)(1 ) 

475 

409 

475 

40 CFR 60 

Rule 2011 

1303(a)(1) 

O2, CO2 , NOx and CO concentrations will be measured using SCAQMD Method 

100.1. These measurements will be made with one of Delta's mobile emission 

measurement laboratories. The system consists of a stainless steel or glass probe, 

heated Teflon line, moisture removal system, sample pump, sample filter, unheated 

Teflon line, and individual component analyzers. The measured concentrations are 

averaged over each sampling period, then corrected for system bias and analyzer drift. 

All quality assurance procedures required by SCAQMD Method 100.1 will be 

performed including pre- and post-test Calibration Error, Sample System Bias and 

Analyzer Drift. 

The sampling will be performed using a 12-point traverse at each test condition 

(or a single point if previous testing demonstrates the absence of significant stratification 

(less than 10% or less than 1 ppm). At the full load condition, the compliance test may 

be performed concurrently with the Relative Accuracy Test Audit (RATA). In this case, 

data from the RATA may be used to demonstrate compliance with the NOx and CO 

emission limits. NOx concentrations will be measured on a 0-5 ppm range. CO 

concentrations will be measured on a 0-10 ppm range. CO2 concentrations will be 

measured on a 0-10% range. O2 concentrations will be measured on a 0-20% range. 

The measured concentrations are averaged over each sampling period, then corrected 

R021 0458-R 1 8 DeltalJ.. 

......... ...-.~-
for system bias and analyzer drift. The drift and bias corrected result will then be used to 

calculate NO, emissions in units of ppm, ppm corrected to 15% O2 , pounds per hour, 

pounds per million Btu, and pounds per million standard cubic feet of natural gas. 

3.2 NH3 BY SCAQMD METHOD 207.1 

Duplicate flue gas samples will be collected non-isokinetically at each test 

condition using a SCAQMD Method 207.1. A 12-point traverse will be performed during 

each NH3 slip test unless previous tests demonstrate the absence of significant NO, 

stratification, then single point sampling will be performed. The sample gas is drawn 

through a glass probe, Teflon sample line, two impingers each containing approximately 

100 ml of 0.1 N H2S04 , an empty impinger, an impinger containing silica gel, and a dry 

gas meter. The optional nozzle and filter will not be used since the units are natural gas 

fired. The contents of the probe, sample line and the first three impingers are recovered 

and analyzed by SCAQMD Method 207.1 for ammonia concentration using the Ion 

Specific Electrode technique. One reagent blank sample and one field blank sample will 

be analyzed. Ammonia slip will be reported in units of ppm, corrected to 15% O2 . 

The tests will be performed over a period of at least 60 minutes. 

3.3 SOx BY SCAQMD METHOD 307.91 

Oxides of sulfur will be measured using SCAQMD Method 307-91 . Two fuel 

samples will be collected in a Tedlar bag and sent to Say bolt Laboratory for Sulfur 

analysis as total reduced sulfur as H2S. 

3.4 ROG BY MODIFIED SCAQMD METHOD 25.3 

Sampling and analyses are performed using Modified SCAQMD Method 25.3 

procedures. The sample apparatus and analyses are provided by Atmospheric Analysis 

and Consulting (AAC) in Ventura California. 

At each test condition, triplicate flue gas samples are extracted sequentially from 

four points (one per port) in the stack through pre-cleaned (high temperature 

conditioned) stainless steel probes connected to an out-of-stack flow controller, into 

stainless steel Summa polished canisters. The flow controller is set to fill the evacuated 

canister to a pressure of -400 mm Hg over a period of a period of one hour. 

Modifications to the Method 25.3 sampling procedures suggested or accepted by 

SCAQMD are: 

• Elimination of the in-stack filter 

• Elimination of the water vial portion of the 25.5 equipment 

• The final pressure in the Summa Canisters is maintained at between 400 and 

500 mm HG (10 - 14 in. Hg) absolute. 

R021 0458-R 1 9 

Dell8!'3. 

.. _--
Figure 3-1 presents a schematic drawing of the sample apparatus. 

FIGURE 3-1 

MODIFIED SCAQMD METHOD 25.3 SAMPLING APPARATUS 

Filter Probe 

Flow Controller 

The samples are analyzed for NMNEOC (Non-Methane Non-Ethane Organic 

Compounds, i.e. Reactive Organic Compounds ROG) using modified SCAQMD Method 

25.3 TCA procedures. Analysis consists of a fore-flush and back-flush of a gas 

chromatography (GC) column, followed by an oxidizer, a methanizer, and a flame 

ionization detector (FlO). The GC separates the NMNEOC from other constituents of the 

sample (methane, ethane, CO2, H20, O2 , N2 , etc.). The oxidizer converts the NMNEOC 

to carbon dioxide. The methanizer converts the resulting CO2 to methane. The methane 

content is detected by the FlO as ppmcarbon. 

R021 0458-R 1 10 
Modifications suggested by SCAQMD to the Method 25.3 analytical procedures 

approved for MC under the LAP are: 

• Pressurization of the canisters to 900 mm Hg with Ultra High Purity (UHP) 

helium analyzed/certified to contain less than 0.05 ppmv of total hydrocarbons 

as carbon 

• Analyzing only the Summa canister fraction of the normal 25.3 sample. No 

water vial used in sampling, no water vial analysis. 

• Utilization of a larger (-2 ml) sampling loop 

• Development of a custom low level (0.1 - 5.0 ppmV propane) calibration 

curve 

• Performance of a Minimum Detection Limit (MOL) study 

• Determination of a Practical Quantitation Limit (PQl) from the MOL study 

Results are reported in parts per million by volume as carbon to 2 significant 

digits, corrected to 15% O2 using the O2 from the canister analysis. The average of the 

results for the duplicate samples is compared to the Emission Standard for determination 

of the compliance status. 

Note: The following message was received on November 9, 2012 and the 

content was incorporated into this protocol; 

From: Roy Olivares [mailto:ROlivares@aqmd.gov] 

Sent: Friday, November 09, 2012 10:19 AM 

To: Mark McDaniels 

Subject: Revised voe testing, condition D29.1 

Mark 

The current voe section of D29.1 is the following 

For natural gas fired turbines only, voe compliance 

shall be demonstrated as follows: a) Stack gas samples are 

extracted into Summa canisters maintaining a final 

canister pressure between 400-500 mm Hg absolute, b) 

Pressurization of canisters are done with zero gas 

analyzed/certified to contain less than 0.05 ppmv total 

hydrocarbon as carbon, and c) Analysis of canisters are per EPA 

Method TO-12 (with pre concentration)and temperature of 

canisters when extracting samples for analysis is not below 70 

deg F. 

The use of this alternative method for voe compliance 

determination does not mean that it is more accurate than AQMD 

Method 25.3, nor does it mean that it may be used in lieu of 

R0210458·R1 Deltab. ... _-........... 11 
AQMD Method 25.3 without prior approval except for the 

determination of compliance with the VOC BACT level of 2.0 

ppmv calculated as carbon for natural gas fired turbines. 

Mike Garibay from source testing has proposed the following VOC 

testing 

For natural gas fired turbines only, VOC compliance shall be 

demonstrated as follows an alternative to AQMD Method 25 . 3 for the 

purpose of demonstrating compliance with BACT as determined by 

CARB and AQMD, may be the following : a) Triplicate S stack gas 

samples are extracted directly into Summa canisters, maintaining a 

final canister pressure between 400-500 mm Hg absolute, b) 

Pressurization of the Summa canisters are is done wi th zero gas 

analyzed/certified to containing less than 0.05 ppmv total 

hydrocarbons as carbon, and c) Analysis of Summa canisters are is 

per unmodified EPA Method TO - 12 (with preconcentration) or the 

canister analysis portion of AQMD Method 25.3 wi th a minimum 

detection limit of 0.3 ppmvC or less and reported to two 

significant figures, and (d) The temperature of the Summa 

canisters when extracting samples for analysis is not to be below 

70 degrees Fahrenheit. 

The use of this alternative method for VOC compliance 

determination does not mean that i t is more accurate than 

unmodified AQMD Method 25.3, nor does it mean that it may be used 

in lieu of AQMD Method 25.3 without prior approval, except for the 

determination of compliance with the VOC BACT level of 2.0 ppmv 

VOC calculated as carbon set by CARE for natural gas fired 

turbines. 

please have the voc tes ting portion of the source test protocol 

address the above changes 

roy 

Roy Olivares 

Air Quality Engineer II 

Energy and Public Service Team 

South Coast Air Quality Management District 

21865 Copley Drive 

Diamond Bar, CA 91765 

909 - 396-2208 

R0210458·R1 12 
3.5 PM BY SCAQMD METHOD 5.1 

Particulate matter will be measured using EPA Method 201A in conjunction with 

SCAQMD Method 5.1. SCAQMD Method 5.1 is cited as the Table in Condition D29.1 

lists District Method 5. District Method 5.1 measures total particulate. This total 

particulate measurement could include material >10 microns. Use of the cyclone as in 

201A will prevent overstating of PM10 emissions if all of the PM emissions from these 

units are not PM1o• A single test will be performed at each of the three conditions; 100%, 

75%, and 50% load conditions. Flue gas is drawn through a stainless steel nozzle, glass 

or stainless steel probe, unheated Teflon line followed by four impingers. Impingers #1 

and #2 contain approximately 100 ml of deionized water, impinger #3 is empty, and 

impinger #4 contains silica gel. A backup filter is placed between impingers #3 and #4. 

The sample will be collected isokinetically (90 - 110%) using a 24-point traverse at the 

exhaust stack location. Each point will be sampled for 10 minutes resulting in a 240 

minute sample time per test. Figure 3-3 presents a diagram of the sampling system. 

R021 0458-R 1 13 8e/laJ1. "---
Temperature 

~-Pitot Tube 

s-Type Pitot Tube ~ 

FIGURE 3-3 

SCAQMD METHOD 5.1 SAMPLE SYSTEM 

Manometer 

Orifice 

Connecting 

Tubing 

Dry Gas 

Meter 

Filter Temperature 

Sensor 

Empty 

Vacuum 

Gauge 

The sample is recovered in two fractions: 1) nozzle, probe, connecting line and 

impinger rinse (01 water) and 2) backup filter. Filter weight gain and water solution 

weight gain are each determined gravimetrically. 

R0210458-R1 14 De/fat.. ""---
4.0 REPORTING 

Following the test. a report will be generated which documents the results of the 

tests. The report will be prepared using the following basic outline: 

I. Title page 

A. Report Title 

B. Prepared For: 

C. For Submittal To: 

D. Prepared By: 

E. Date 

F. Report Number 

II. Review Page 

A. Signatures of person who prepared the report and signature of person 

who reviewed the report 

II I. Table of Contents 

IV. Introduction and Summary 

A. Identifies the client. source, reason for the test, test date(s), test 

personnel, client/source personnel 

B. Presents a summary of the test results 

C. Outlines the organization of remainder of the report. 

V. Unit Description 

A. Process description 

B. Control equipment description 

C. Sample location(s) description 

D. Unit operating condition(s) during the test 

VI. Test Description 

A. Test methods, replicates, duration, calculations 

VII. Test Results and Evaluation 

A. Re-states the results of the test 

B. Results tables with more detail on individual test runs and supporting data 

C. Evaluation of the test results and data validity 

VII I. Appendices 

A. Test Data 

R021 0458-R 1 15 De//a11 

"'---
1. Data Sheets/Stripcharts 

2. Laboratory Data 

3. Quality Assurance Data 

B. Process data 

1. Unit and control equipment operating data 

C. Calculations 

D. Quality Assurance Program Summary 

R021 0458-R 1 16 1Ie//a!1 

........ _-
APPENDIX A QUALITY ASSURANCE 

R021 0458-R 1 A-1 Deltal1 "'-.--
QUALITY ASSURANCE PROGRAM SUMMARY 

Delta Air Quality Services, Inc. is committed to providing emission related data 

which is complete, precise, accurate, representative, and comparable. Delta's quality 

assurance program and procedures are designed to ensure that the data meet or exceed 

the requirements of each test method for each of these items. The quality assurance 

program consists of the following items: 

• Assignment of an Internal QA Officer 

• Development and use of an internal QA Manual 

• Personnel training 

• Equipment maintenance and calibration 

• Knowledge of current test methods 

• Chain-of-custody 

• QA reviews of test programs 

Assignment of an Internal QA Officer: Delta has assigned an internal QA Officer who is 

responsible for administering all aspects of the QA program. 

Internal Quality Assurance Manual: Delta has prepared a QA Manual according to the 

guidelines issued by EPA. The manual documents and formalizes all of Delta's QA 

efforts. The manual is a "living" document which is revised as Delta adds capabilities and 

procedures. The QA manual provides details on the items provided in this summary. 

Personnel Training: Personnel training is essential to the production of high quality test 

results. Delta's training programs include: 

• A requirement for all technical personnel to read and understand the test 

methods performed 

• A requirement for all technical personnel to read and understand the Delta QA 

manual 

• In-house training 

• Quality Assurance meetings 

• Attendance at EPA sponsored training courses 

• Maintenance of training records. 

Equipment Maintenance and Calibration: All laboratory and field equipment used as a 

part of Delta's emission measurement programs is maintained according to 

manufacturer's recommendations. A summary of the major equipment maintenance 

schedules is summarized in Table A-1 . In addition to routine maintenance, calibrations 

are performed on all sampling equipment according to the procedures outlined in the 

applicable test method. The calibration intervals and techniques for major equipment 

components is summarized in Table A-2. 

Knowledge of Current Test Methods: Delta maintains current copies of EPA, ARB, and 

SCAQMD Source Test Manuals and Rules and Regulations. Delta personnel coordinate, 

attend, and present papers at emission testing related conferences. Delta personnel 

maintain memberships in the Air and Waste Management Association and Source 

R0210458-R1 A-2 De/tab. ----
Evaluation Society. Delta personnel continually work with industry and regulatory 

agencies in monitoring and developing new methods and rules. 

Chain-of-Custody: Delta maintains chain-of-custody documentation on all data sheets 

and samples. Samples are stored in a locked area accessible only to Delta source test 

personnel. Data sheets are kept in the custody of the originator, program manager, or in 

locked storage until return to Delta's office. Upon return to the office, copies are made 

and stored in a locking file. The original data sheets are used for report preparation and 

any additions are initialed and dated. 

QA Reviews: Every Delta report is reviewed by someone separate from the report 

author. The reviewer is selected based on knowledge of the test methods used and the 

source tested. Periodic field, laboratory, and report reviews are performed by the QA 

Officer. Test plans are reviewed to ensure proper test methods are selected and reports 

are reviewed to ensure that the methods were followed and any deviations from the 

methods are justified and documented. 

R02 10458-R1 A-3 861f11b.. 

............... -
TABLE A-1 

EQUIPMENT MAINTENANCE SCHEDULE 

Equipment 

Pumps 

Flow Meters 

Sampling Instruments 

Acceptance Limits 

1. Absence of leaks 

2. Ability to draw 

manufacturers 

required vacuum 

and fiow 

1. Free mechanical 

movement 

1. Absence of 

malfunction 

2. Proper response to 

zero, span gas 

Integrated sampling 1. Absence of leaks 

tanks 

Mobile van sampling 1. Absence of leaks 

system 

Sampling lines 

R0210458-R1 

1. Sample 

degradation less 

than 2% 

A-4 

Frequency of Service 

Every 500 hours of 

operation or 6 months, 

whichever is less 

Every 500 hours of 

operation or 6 months, 

whichever is less 

As recommended by 

manufacturer 

Methods of Service 

1. Visual inspection 

2. Clean 

3. Replace parts 

4. Leak check 

1. Visual inspection 

2. Clean 

3. Calibrate 

As recommended by 

manufacturer 

Depends on nature of 1. Steam clean 

use 2. Leak check 

Depends on nature of 1. Change filters 

use 2. Change gas dryer 

3. Leak check 

4. Check for system 

contamination 

After each test series 1. Blow dry, inert gas 

through line until 

dry. 

Delta/j. 

....... ~--
TABLE A-2 

MAJOR SAMPLING EQUIPMENT CALIBRATION REQUIREMENTS 

Sampling Equipment Calibration Frequency Calibration Procedure Acceptable Calibration 

Criteria 

Continuous Analyzers Before and after each 3-point calibration error < 2% of analyzer range 

test day test 

Continuous Analyzers Before and after each 2-point sample system < 5% of analyzer range 

test run bias check 

Continuous Analyzers After each test run 2-point analyzer drift < 3% of analyzer range 

determination 

CEMS System Beginning of each day leak check < 1 in. Hg decrease in 5 

min. at> 20 in. Hg 

Continuous Analyzers Daily 3-point linearity < 1 % of analyzer range 

NO, Analyzer Daily N02 -> NO converter > 90% 

efficiency 

S-type pitot tube Semi-annually Dimensional calibration Meet dimensional 

criteria of Method 2 

S-type pitot tube Annually Wind tunnel calibration Defined in Method 2 

S-type pitot tube Prior to each project Visual inspection Meet dimensional 

criteria of Method 2 

Differential Pressure Semi-annually Correction factor based +/- 5% 

Gauges (except for on 5-point comparison to 

manometers) standard 

Differential Pressure Bi-monthly 3-point comparison to +/-5% 

Gauges (except for standard, no correction 

manometers) factor 

Manometer Semi-annually Clean and replace fluid 

Barometer Semi-annually Adjusted to mercury-in- +/- 0.1 inches Hg 

glass or National 

Weather Service Station 

Dry gas meter Semi-annually Calibration check at 4 +/-2% 

flow rates using a NIST 

traceable standard 

Dry gas meter Bi-monthly Calibration check at 2 +/- 2% of semi-annual 

flow rates using a NIST factor 

traceable standard 

Dry gas meter orifice Annually 4-point calibration for 

l1H@ 

Temperature sensors Semi-annually 3-point calibration vs. +/- 1.5% 

NIST traceable standard 

R0210458-Rl A-5 
APPENDIXB TEST METHODS 

R021 04S8-R 1 B-1 1161111'1 

.. _--
SCAQMD METHOD 100.1 CALIBRATION SEQUENCE AND CALCULATIONS 

DEFINITIONS: 

1) Analyzer Calibration: 

2) Calibration Error: 

3) Analyzer Linearity: 

4) Sample System Bias: 

R0210458-R1 

Zero and span gas(es) are introduced directly to the 

analyzer. Adjustments are made to the analyzer zero and 

upscale readings, as necessary to match the certified 

concentrations of the calibration gas. 

Zero, mid (40-60% of full scale), and high (80-100% of full 

scale) calibration gases are introduced directly to the 

analyzer and the analyzer response to each gas is 

recorded (without adjustment to the analyzer). The 

Calibration Error (difference between the analyzer response 

to the calibration gas and the certified concentration of the 

calibration gas) must not exceed ±2% of the analyzer full 

scale for any of the three gases. 

Analyzer linearity is defined as the difference between an 

analyzer response to the mid range gas and the predicted 

analyzer response to the mid range gas based on the 

analyzer response to the zero and high range gas. The 

Analyzer Linearity test is required on a semi-annual basis 

and must not exceed ±1 % of the analyzer range. It should 

be noted that this linearity requirement is more stringent 

than the best available calibration standards (+/-2%) for the 

low CO and NO, concentrations expected during this test 

program. For this reason, an analyzer linearity of less than 

2% will be considered as acceptable for this program. 

The sample system bias test involves introducing zero and 

one upscale (mid or high) calibration gas to the entire 

sampling system and recording the analyzer response. The 

analyzer response to the calibration gas after it has passed 

through the entire sample system is compared to the 

analyzer response to same the calibration gas injected 

directly to the analyzer. The test is used to determine the 

effect which the sample system has on the species of 

interest and correct the measured values for any effect 

which the system has. The sample system bias is required 

to be less than ±5% of the analyzer range for both the zero 

and upscale gas. 

B-2 Del/a~ "---
PROCEDURES AND CALCULATIONS: 

Figure 1 presents a flow chart for the SCAQMD Method 100.1 calibration 

sequence. All calibrations are documented as one-minute averages from the reference 

method Data Acquisition System. 

Following assembly of the system, analyzer warm up time, and a successful leak 

check of the sample system, the calibration/test sequence presented in Figure 1 can 

begin. 

An Analyzer Calibration is performed as necessary by adjusting the zero and 

span settings of the analyzer. These calibrations are not necessarily recorded on the 

chart recorder. Calibration Error is then determined at three levels for each range (which 

is expected to be used) of each analyzer. This check is performed, at a minimum, once 

at the beginning and once at the end of each test day. The calibration error must not 

exceed ±2% of the full range of the analyzer as determined by the following equation: 

Calibration Error Analyzer Response- Cal. Gas Value * 100% 

Analyzer Range 

The data from the Calibration Error test can be used to determine Analyzer 

Linearity. The analyzer response to the mid gas is predicted using linear regression and 

the analyzer response to the zero and high calibration gas and the zero and high 

calibration gas values. The analyzer linearity must be demonstrated on a semi-annual 

basis using the following equation: 

Analyzer Linearity = 

where: 

Analyzer Response - Predicted Response 

Analyzer Range 

* 100% 

Response to High Gas - Response to Zero Gas 

Predicted Response :;: .. Mid Gas Value + Response to Zero Gas 

High Gas Value 

The Sample System Bias test is performed before and after each test run and 

must not exceed ±5% of the analyzer range for both the zero and upscale span gas. The 

system bias is calculated using the following equation: 

Response to System Bias - Response to Analyzer Cal Sample System Bias = * 100% Analyzer Range 

R021 0458-R 1 B-3 /lell8l:1 

....... ~--
where: 

Response to Analyzer Cal = The analyzer response to the last time the same 

calibration gas was introduced directly to the analyzer (this may be the pre-test 

calibration error value or a more recent analyzer calibration adjustment) 

Zero and Calibration Drift are calculated for each test run based on the analyzer 

response during the pre- and post-test sample system bias test. Zero and upscale drift 

must not exceed ±3% of the analyzer range. 

I ·f Post- Test System Bias Resonse - Pre - Test System Bias Response Ana yzer Dn t = • 100% 

Analyzer Range 

The pre- and post-test analyzer response during the sample system bias test are 

used to correct the raw test average for any sample system bias and analyzer drift. The 

drift/bias corrected data are the actual reported concentrations and are used for 

subsequent calculations (mass emission rates, Ib/MMBtu, corrections to 3% or 15% O2, 

etc.). The drift/bias corrections is performed using the following equation: 

c-c c = o. C c C _ C ma m 0 

where: 

Cc = Drift/bias corrected concentration 

C = Raw Test Average 

Cm = Average of pre- and post-test response to sample system bias span 

Co = Average of pre- and post-test to sample system bias zero 

Cma = Span gas value 

ADDITIONAL QUALITY ASSURANCE CHECKS: 

SCAQMD Method 100.1 specifies the allowed analyzer interferences for each 

analyzer type. No interference checks are required for O2 or NO, analyzers. 

Interference tolerances are given for CO, CO2, and S02 analyzers. The analyzers used 

by Delta are certified by the manufacturers to have interference responses which meet 

the requirements of Method 100.1. 

SCAQMD has published a draft method for determining the efficiency of a N02 to 

NO converter. This test will be performed once on the day of the test. The converter 

efficiency must be 90% or greater. 

R021045B-R1 8-4 De/tab. "'-. ....... -
Analyzer 

Cal 

Cal No 

Error < 2% 

No 

Yes /Yes 

System No System IBias < 5% Problem? 

Yes 

Don't Know Stratified No 

Location? 

Yes 

Multi-Point Single Point 

Test Test 

! . System No 

Bias < 5% 

Yes 

Cal No 

Drift < 3% 

Yes 

Note: AQMD policy allows multiple Another No Analyzer Cal test runs to be validated by one set 

of pre- and post-test sample system Test? (if necessary) 

bias tests as long as the bias ! checks are performed within 2 hours Yes 

of the previous bias check. No No 

Analyzer Cal 

Cal? Error < 2% 

Yes 

No ! Yes 

Yes System [ Finish 

Bias < 5% t- ) 

FIGURE 1: SCAQMD METHOD 100.1 CALIBRATION AND TEST SEQUENCE 

R021 0458-R 1 8-5 .. Delfal'1 _ ......... -
Temperature 

S Probe 

~ Pltot Tube 

/ 

S-Type Pitot Tube 

R021 0458-R 1 

Manometer 

Orifice 

Connecting 

Teflon TUbing 

Temperature 

Dry Gas 

Meter 

Filter Temperature 

Valve 

SCAQMD METHOD 5.1 SAMPLING TRAIN 

8-6 
Filter Probe 

Flow Controller 

MODIFIED SCAQMD METHOD 25.3 SAMPLING APPARATUS 

R021 0458-R 1 8-7 1le1/a!1. 

....... -.-
APPENDIX C CALCULATIONS 

R021 0458-R 1 C-1 IJeltal1 ""---
GENERAL EMISSION CALCULATIONS 

1) Stack Gas Velocity 

A. Stack gas molecular weight, Ibllb-mole 

MWdry = 0.44 * %C02 + 0.32 * %02 + 0.28 * %N2 

MWwet = MWdry * (1-Bwo) + 18 * Bwo 

B. Absolute stack pressure, iwg 

Ps = Pbar + Psg 

13.6 

c. Stack gas velocity, ftIsec 

Vs = 2.9 * Cp * .J!).p *.JT: * 

2) Moisture 

A. Sample gas volume, dscf 

Vmstd = 0.03342 * Vm * (Pbar + 

B. Water vapor volume, scf 

v = 0.0472 * V. * Tref 

wstd Ie 528 oR 

29.92 * 28.95 

Ps * MWwet 

c. Moisture content, dimensionless 

3) Stack gas volumetric flow rate 

A. Actual stack gas volumetric flow rate, wacfm 

Q = V * A * 60 s s 

B. Standard stack gas flow rate, dscfm 

R021 0458-R 1 C-2 8e//a/1 

.. _--
Q = Q * (1- B ) * T,er * Ps 

sd we Ts 29.92 

4) Gaseous Mass Emission Rates. Ib/hr 

M = ppm * MIJII; * QSd • 60 

SV * 106 

5) Emission Rates. Ib/MMBtu 

Ib _ ppm * MIJII; * F * 20.9 

MMBtu - SV*106 20.9-%0, 

6) Emission Factor. Ib/MMSCF 

Ib Ib *HHV 

MMSCF MMBtu 

VI. Percent Isokinetic 

17.32 x T, (Vm std) 528 e R /- x---- - (1- Bwo)O x V, x Ps x Dn' T,..! 

VII. Particulate emissions 

a) Grain loading, gr/dscf 

C = 0.01543 (M,/V m SId) 

b) Grain loading at 12% CO" gr/dscf 

C12% co, = C (121% CO,) 

c) Grain loading at 3% 0" gr/dscf 

C3% 0' = C * 17.9/(20.9-%0,) 

d) Mass emissions, Ib/hr 

M = C x Qsd x (60 min/hr)/(7000 gr/lb) 

e) Particulate emission factor 

6 lIb 20 .. 9 

lb / 10 Btu = ex 7000gr x F x 20.9 _ % 0, 

R021 0458-R 1 C-3 
Nomenclature: 

As 

Bwo 

C12%C02 

C3%02 

C 

Cp 

On 

F 

H 

HHV 

I 

Mn 

MI 

MW 

Mwi 

o 

L\P 

Pbar 

Ps 

Psg 

a 

Ows 

Osd 

SV 

Tm 

Tret 

T, 

Vs 

Vic 

Vm 

Vm'td 

VWStd 

Yd 

R021 0458-R 1 

= stack area, ft2 

= flue gas moisture content, dimensionless 

= particulate grain loading, gr/dscf corrected to 12% CO2 

= particulate grain loading, gr/dscf corrected to 3% CO2 

= particulate grain loading, gr/dscf 

= pitot calibration factor, dimensionless 

= nozzle diameter, in. 

= fuel F-Factor, dscf/MMBtu @ 0% O2 

= orifice differential pressure, iwg 

= fuel higher heating value, Btu/SCF 

= % isokinetics 

= mass of collected particulate, mg 

= mass emission rate of specie i, Ib/hr 

= molecular weight of flue gas, Ib/lb-mole 

= molecular weight of specie i: 

S02: 64 

NOx: 46 

CO: 28 

HC: 16 

= sample time, min. 

= average velocity head, iwg = (,hp)2 

= barometric pressure, inches Hg 

= stack absolute pressure, inches Hg 

= stack static pressure, iwb 

= wet stack flow rate at actual conditions, wacfm 

= wet stack flow at standard conditions, wscfm 

= dry standard stack flow rate, dscfm 

= s~ecific molar volume of an ideal gas at standard conditions, 

ft lib-mole 

= meter temperature, OR 

= reference temperature, OR 

= stack temperature, OR 

= stack gas velocity, .ft/sec 

= volume of liquid collected in impingers, ml 

= uncorrected dry meter volume, dcf 

= dry meter volume at standard conditions, dscf 

= volume of water vapor at standard conditions, scf 

= meter calibration coefficient 

C-4 De/Ia/:). '"'---" 
APPENDIX D FORMS 

R0210458·Rl D·l 1Ie1/a!:1 

---
South Coast 

Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

(909) 396-2000 ' www.aqmd.gov 

Mr. Robert A. Finken 

Delta Air Quality Services, Inc. 

1845 N. Case Street 

Orange, CA 92865 

Subject: LAP Approval Notice 

Reference # 96LA 1220 

Dear Mr. Finken: 

January 11,2012 

We completed our review of the renewal application you submitted for approval under the South Coast 

Air Quality Management District's Laboratory Approval Program (AQMD LAP). We are pleased to 

inform you that your finn is approved for the perio'd beginning January 31 , 2012, and ending January 31, 

2013 for the following methods: 

SCAQMD Methods 1-4 

SCAQMDMethod 100.1 

SCAQMD Methods 25.1 and 25.3 (Sampling) 

SCAQMD Methods 5.1, 5.2, 5.3, and 6.1 

SCAQMD Rule 1420 - (Lead) Ambient Sampling 

USEPA CTM-030 and ASTM 06522-00 

Thank you for participating in the SCAQMD LAP. Your cooperation helps us to achieve the goal of the 

LAP: to maintain high standards of quality in the sampling and analysis of source emissions. You may 

direct any questions or information to LAP Coordinator, Glenn Kasai. He may be reached by telephone 

at (909) 396-2271, by facsimilie at (909) 396-2099, or via e-mail at gkasai@aqmd.gov. 

RE:GK/gk 

cc: Mike Garibay 

Glenn Kasa.i 

12011 I LapRenewal.doc 

R021 0458-R 1 

s~~~er y & __ _ ;I Ru Eden, Senior Manager 

Laboratory Services & 

Source Test Engineering 

D-2 Ilellal1 

.................. -
::0 

o 

'" ~ 

~ 01 

0> 

;'0 

~ 

o 

W 

II. 

iI

!i;:a 

!~ 

State of California 

Air Resources Board 

Approved Independent Contractor 

Delta Air Quality Services, Incorporated 

This is to certify .Ilia! the compa,ny listed EibQve'hasbeen approved 

by the Air ResoutceS' Board to'conduct eompnance testing 

pursuant to titliH.7,: c'alifornia · Code :pf RegutatIDns', section 91207 

until Ju~30 2013',.fc)r those test methods ~sted below: 

ARB S ... re<: Test Meth~.; 1,2,3,.4,5,.6,'8, 17, 20/ 501 

106'«;0; cO:;. NO" 0" SO,) 

(}L~/f_~ Alberto AY~1.. Ph.D., M.S.E. 

Chief, Monnoring and Laboratory DMsion 
;:0 

a 

N 

~ 

a 

.". 

en 

(l) 

, 

;:0 

~ 

a 

... 

~ IS. 

~ 

State of California 

Air Resources Board 

Approved Independent Contractor 

Delta Air Quality Seni~ Incorporated 

This is to certifyiHat the cOi)1pany liste<) ~bovehas been approved 

by the Air Resolll;Ces:B6ard to'condtictcorrip'!iance testing 

pursuant to titfEiJ1?:;;CallforruaCod!'fPf Ril9U1ations; section 91207 

until June30; 2013;'for those-test.niethOds:i1sted below: 

.~' . . , . ' . ,. ~ ~, '. ,~ " 

• I Visible·Emlw.oD.s Evaluation 

U.S. EPATestMethods 2~lA (1991 ..... ~I, 202.(1991 version) 

.if 

Alberto Ayala.?f>.D .• M.S.E. 

Chief. Monitoring and LaboratOlY Division 
STATEMENT OF NO CONFLICT OF INTEREST AS AN INDEPENDENT 

TESTING LABORATORY 

(To be completed by authorized source testing firm representative and included in source test report) 

The following facility and equipment were tested by my source testing firm, and are the subjects of this 

Statement: 

Facility ID: .,.-,.-____ ='4;::6"'5:;::3=.6 __________________ _ 

Date(s) Tested: _____ T:::e::;s::-t '=P,..la""n::--:-:::--_-=---:---:-__________ _ 

Facility Name: :-____ -:=C7P7-V::::S'7e=7n!!t!!:in!:'e'7'""E~n:!!:e!.lrg:I.JvL!...P!.lro~i"'ec!<lt'--__________ _ 

Equipment Address: 911 Bixby Drive 

City of Industry, California 91748 

Equipment Tested: ___ -:;U'-';n"-;its=''''', 2~',.:3",-, =4,-:' 5::a,-,!6~, .f:7!-" &7:'8-=,--:--:-:; ________ _ 

Device 10, AlN, P/N: ___ ""DC!1"" D~7!..1,..!:D!..l1,"3 ... , ~D~19~'L..!D~2.,5",-, .>1.3.!.J1 ,...,3!,!7 .... , ~&~4~2 ________ _ 

I state, as its legally authorized representative, that the source testing firm of: 

Source Test Firm: Delta Air Quality Services. Inc. 

Business Address: .,!,1 ",84",5,-",N~ . C=as"'e:.;S,..t"'re"'e"'t __________________ _ 

Orange, California 92865-4234 

is an "Independent Testing Laboratory" as defined in District Rule 304(k): 

For the purposes of this Rule, when an independent testing laboratory is used for the purposes 

of establishing compliance with District rules or to obtain a District permit to operate, it must 

meet all of the following criteria: 

(1) The testing laboratory shall have no financial interest in the company or facility being 

tested. or in the parent company or any subsidiary thereof-

(2) The company or facility being tested, or parent company or any subsidiary thereof, 

shall have no financial interest in the testing laboratory; 

(3) Any company or facility responsible for the emission of significant quantities of pollutants to 

the atmosphere, or parent company or any subsidiary thereof shall have no financial interest in 

the testing lab'lratory; and 

(4) The testing laboratory shall not be in partnership with, own or be owned by, in part or in 

full, the contractor who has provided or installed equipment (basic or control), or monitoring 

systems, or is providing maintenance for installed equipment or monitoring systems, for the 

company being tested 

Furthermore, I state that any contracts or agreements entered into by my source testing firm and 

the facility referenced above, or its designated contractor(s), either verbal or written, are not 

contingent upon the outcome of the source testing, or the source testing information provided to 

the SCAQMD .. _______ , 

Signature: L,t- {~j J 1->.. 

Bob Finken 

(Name) 

President 

(Title) 

FORM ST-110 :stevforl.doc (Revised 11/18/98) 

R0210458-R1 0-5 

Date: ___ -'-"2='-17'-'1".20"-'",,2'--___ _ 

714-279-6777 121712012 

(Phone) (Date) 

811/18/1 '"'- - -
APPENDIX E FACILITY PERMIT TO OPERATE CONDITION 029.1 

R038842-R1 E-1 DIlIfa!1 

---
SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 Copley Drive. Diamond Bar. CA 91 765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

Section H Page: 35 

Facilitv 10: 152101 

R~ision# : 0 

Date: April 1S,20ll 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with the terms and conditions set forth below: 

The operator shall also install and maintain a device to continuously record the 

parameter being measured 

The measuring device or gauge shall be accurate to within plus or minus 5 

percent. It shall be calibrated once every twelve months 

It shall be calibrated once every twelve months 

The pressure drop across the catalyst shall not exceed 12 inches water column 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(aXI)-BACT, 12-6-2002; RULE 

1703(aX2) - PSD-BACT, 10-7-1988; RULE 1005, 5-6-1005) 

[Devices subject to this condition : C4, CIO, C16, C22, C28, C34, C40, C46) 

012.5 The operator shall install and maintain a(n) non-resettable elapsed time meter to 

accurately indicate the elapsed operating time from the engine. 

[RULE 1110.2,2-1-2008; RULE 1303(b)(2)-Offset, 5-10-1996; RULE 1303(bX2) 

-Offset, 12-6-2002; RULE 1470,6-1-2007; RULE 1012, S-6-100S) 

[Devices subject to this condition : 049) 

D29.1 The operator shall conduct source testes) for the pollutant(s) identified below. 

Pollutant(s) to I Required Test Methodes) I Averaging Time I Test Location 

be tested 

NOX emissions District method 100.1 1 hour Outlet of the SCR 

serving this equipment 

CO emissions I District method 100.1 I I hour I Outlet of the SCR 

serving this equipment 

SOX emissions I AQMD Laboratory 

Method 307-91 

I Not Applicable I Fuel sample 

voe emissions I District Method 25.3 I 1 hour I Outlet of the SCR 

serving this equipment 
SOllTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 Copley Drlve. Diamond Bar. CA 91 765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

SeClion H 

Facility 10: 

Revision ' : 

Date: 

Page: 36 

IS2707 

o 

April 15.2011 

SECTIONH: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with the terms and conditions set forth below: 

PM I 0 I District Method 5 

emissions 

NH3 emissions I District method 207.1 

and 5.3 or EPA method 

17 

I 4 hours 

II hour 

I Outlet of the SCR 

serving this equipment I Outlet of the SCR 

serving this equipment 
• ~i~ •. l~~L 

SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT 

21865 Copley Drive, Diamond Bar, CA 91 765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

Section H Page: 37 

FacilitY 10: 152707 

Revision II: 0 

Date: April IS. 2011 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with the terms and conditions set forth below: 

The test shall be conducted after AQMD approval of the source test protocol, but 

no later the later of 180 days after initial start-up or three hundred hours of 

operations after start-up. The AQMD shall be notified of the date and time of the 

test at least 10 days prior to the test 

The test shall be conducted to detennine the oxygen levels in the exhaust. In 

addition, the tests shall measure the fuel flow rate (CFH), the flue gas flow rate, 

and the turbine generating output in MW. 

The test shall be conducted in accordance with AQMD approved test protocol. 

The protocol shall be submitted to the AQMD engineer no later than 45 days 

before the proposed test date and shall be approved by the AQMD before the test 

commences. 

The test protocol shall include the proposed operating conditions of the turbine 

during the tests, the identity of the testing lab, a statement from the testing lab 

certifYing that it meets the criteria of Rule 304, and a description of all sampling 

and analytical procedures 

The test shall be conducted when this equipment is operating at maximum, 

average, and minimum loads. 

For natural gas fired turbines only, VOC compliance shall be demonstrated as 

follows: a) Stack gas samples are extracted into Summa canisters maintaining a 

final canister pressure between 400-500 mm Hg absolute, b) Pressurization of 

canisters are done with zero gas analyzed/certified to contain less than 0.05 ppmv 

total hydrocarbon as carbon. and c) Analysis of canisters are per EPA Method 

TO-12 (with pre concentration) and temperature of canisters when extracting 

samples for analysis is not below 70 deg F. 

The test shall be conducted for compliance verification of the BACT VOC 2.0 

ppmv limit. 

The test results shall be reported with two sil\llificant dip;its. 
SOlITH COAST AIR QUALITY MANAGEMENT DISTRlcr 

21865 Copley Drive, Diamond Bar, CA 91 765 

FACILITY PERMIT TO OPERATE 

CPV SENTINEL LLC 

SectiDn H Page; 31 

Facility ID: 152707 

Revision II: 0 

o.tc: AprillS,2011 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERATE 

The operator shall comply with tbe terms and conditions set forth below: 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(aXI)-BACT, 12-6-2002; RULE 

1303(b)(Z}-Oft'aet, 5-10-1996; RULE 1303(b)(2}-Offset, 12-6-2002; RULE 1703(a)(2)-

PSD-BACT, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: 01, 07, 013, 019, 025, 031, 037, 043] 

029.2 The operator shall conduct source testes) for the pollutant(s) identified below. 

Pollutant(s) to 

be tested 

NH3 emissions 

I Required Test Method(s) 

I District method 207.1 

and 5.3 or EPA method 

17 

I Averaging Time 

11 hour 

I Test Location 

I Outlet of the SCR 

serving this equipment 

The test shall he conducted and the results submitted to the District within 45 

days after the test date. The AQMD shall be notified of the date and time of the 

test at least 7 days prior to the test. 

The test shall be conducted at least quarterly during the first twelve months of 

operation and at least annually thereafter. The NOx concentration, as determined 

by the CEMS, shall be simultaneously recorded during the ammonia slip test. If 

the CEMS is inoperable, a test shall be conducted to determine the NOx 

emissions using District Method 100.1 measured over a 60 minute averaging time 

period. 

If the turbine is not in operation during one quarter, then no testing is required 

during that quarter 

The test shall be conducted to demonstrate compliance with the Rule 1303 BACT 

concentration limit 

[RULE 1303(a)(1}-BACT, 5-10-1996; RULE 1303(aXI}-BACT, 12-6-2002] 

[Devices subject to this condition: Dl, 07, 013, 019, 025, D31, 037, 043] 
END OF DOCUMENT