Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 2516 56505 National Grid Generation, LLC National Grid Generation, LLC

legal owner175 East Old Country Road Hicksville NY 11801 2517 56505 National Grid Generation, LLC National Grid Generation, LLC

legal owner175 East Old Country Road Hicksville NY 11801

Page 1Facility _Information plant_name

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip Northport Eatons Neck Road Northport NY 11768 Environmental Management175 East Old Country Road Hicksville NY 11801 Port Jefferson

Beach Street

Port Jefferson

NY 11777 Environmental ManagementNational Grid175 East Old Country Road Hicksville NY 11801

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No FALSE TRUE TRUE FALSE TRUE FALSE TRUE TRUE No FALSE TRUE TRUE FALSE TRUE FALSE TRUE TRUE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE TRUE Quarterly Excess Emission Reports are required for opacity and for Northport Unit 4 (Subpart D-opacity, NOX and sulfur in fuel) No Part I General Facility InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi FALSE TRUE Part I General Facility InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 4Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 5Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 6Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 7Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 8Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 9Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 10Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 11Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 12Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 13Facility _Information Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 800F and 1000F. The value of 900F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1600 and 2400 psi. The value provided of 2000 psi is an average value.8)The original design gross boi Part I General Facility

InformationEIA Utility Code - On April 1, the DOE changed the utility code from 26751 (KeySpan Generation, LLC) to 56505 (National Grid Generation, LLC)Question 15 Boiler Information1)Since all four units are cabable of combusting both oil and natural gas, the values provided are averages between the oil and gas firing conditions.2)The difference between the design heat input value and the maximum heat input value are due to unit inefficienies.3)The design steam pressure and the design steam temperature is a single point value used in the original design of the boiler.4)The operating steam (main steam) temperature varies between 950F and 1000F. The value of 975F is an average value.5)The reheat steam temperature varies between 900F and 1000F. The value of 950F is an average value.6)The steam pressure is at the throttle location.7)The steam pressure varies between 1300 and 1900 psi. The value provided of 1600 psi is an average value.8)The original design gross boi

Page 14facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 2516 1 Manger, Air Quality Compliance Cathy Waxman 5165452579 cathy.waxman@us.ngrid.com TRUE 2517 2 Manager, Air Quality Compliance Cathy Waxman 5165452579 cathy.waxman@us.ngrid.com TRUE

Page 15facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note

Page 16facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type 2516 No.6 Fuel Oil (residual or bunker C) 98 99 2516 other (specify) 2 1 Waste oil and boiler cleaning solution 2517 No.6 Fuel Oil (residual or bunker C) 99 100 2517 other (specify) 1 0 Boiler cleaning solution

Page 17facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 2516 Boiler Cleaning Solutions

TRUE TRUE 284429 num ber/year 2009 gallons/yr

No The decision to continue to utilize this material will be dependent on the requirements of the final regulations 2516 Waste Fuel TRUE TRUE 757750 num ber/year 2009 gallons/yr

No The decision to continue to utilize this material will be dependent on the requirements of the final regulations 2517 Boiler Cleaning Solution

TRUE TRUE 179857 num ber/year 2009 gallons per year

No The decision to continue to utilize this material will be dependent on the requirements of the final regulation. 2517 Waste Fuel TRUE TRUE 0 num ber/year 2009 gallons/yr

No The decision to continue to utilize this material will be dependent on the requirements of the final regulation.

Page 18facility _other_materials rcra_explain The decision to continue to utilize this material will be dependent on the requirements of the final regulations The decision to continue to utilize this material will be dependent on the requirements of the final regulations The decision to continue to utilize this material will be dependent on the requirements of the final regulation. The decision to continue to utilize this material will be dependent on the requirements of the final regulation.

Page 19boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 2516 1 Tangential firing Dry Bottom fuel oil 3550 3650 375 2516 2 Tangential firing Dry Bottom fuel oil 3550 3650 375 2516 3 Tangential firing Dry Bottom fuel oil 3550 3650 375 2516 4 Tangential firing Dry Bottom fuel oil 3550 3650 375 2517 3 Tangential firing Dry Bottom coal 1800 1850 190 2517 4 Tangential firing Dry Bottom coal 1800 1850 190

Page 20boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 363 84 83 2400 2000 1005 975 FALSE 1005 363 84 83 2400 2000 1005 975 FALSE 1005 363 84 83 2400 2000 1005 975 FALSE 1005 363 84 83 2400 2000 1005 975 FALSE 1005 181 84 83 1800 1600 1005 975 FALSE 1005 181 84 83 1800 1600 1005 975 FALSE 1005

Page 21boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 900 5636 37.2 N FALSE FALSE 900 5198 29.8 N FALSE FALSE 900 4784 27.7 N FALSE FALSE 900 6372 38 Subpart D FALSE FALSE 950 5245 27.8 N FALSE FALSE 950 4790 26.9 N FALSE

Page 22boiler_information

NOx_control

SO2_control

combustion_additives Yes Yes No Yes Yes No Yes Yes No Yes Yes No Yes Yes No Yes Yes No

Page 23boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 2516 1 natural gas 2007 96.57 58.882 2516 1 natural gas 2008 99.287 87.747 2516 1 natural gas 2009 99.508 91.12 2516 1 oil - other 2007 0.01 0.004 Waste fuel and boiler cleaning solutions 2516 1 oil - other 2008 0.011 0.011 Waste fuel and boiler cleaning solution 2516 1 oil - other 2009 0.001 0.01 Waste fuel 2516 1 oil - residual or bunker 2007 3.42 41.114 2516 1 oil - residual or bunker 2008 0.702 12.242 2516 1 oil - residual or bunker 2009 0.491 8.87 2516 2 natural gas 2007 90.768 33.264 2516 2 natural gas 2008 96.095 55.6 2516 2 natural gas 2009 97.85 69.9 2516 2 oil - other 2007 0.001 0.006 Waste fuel 2516 2 oil - other 2008 0.017 0.1 Waste fuel and boiler cleaning solution 2516 2 oil - other 2009 0.02 0.1 Waste fuel and boiler cleaning solution 2516 2 oil - residual or bunker 2007 9.231 66.73 2516 2 oil - residual or bunker 2008 3.888 44.3 2516 2 oil - residual or bunker 2009 2.13 30 2516 3 natural gas 2007 79.667 16.572 2516 3 natural gas 2008 95.498 51.82 2516 3 natural gas 2009 97.783 69.313 2516 3 oil - other 2007 0.007 0.022 Waste fuel 2516 3 oil - other 2008 0.003 0.025 Waste fuel 2516 3 oil - other 2009 0.025 0.04 Waste fuel and boiler cleaning solution 2516 3 oil - residual or bunker 2007 20.326 83.406 2516 3 oil - residual or bunker 2008 4.499 48.155 2516 3 oil - residual or bunker 2009 2.192 30.647 2516 4 natural gas 2007 97.309 64.87 2516 4 natural gas 2008 97.334 65.035 2516 4 natural gas 2009 98.57 77.915 2516 4 oil - other 2007 0.078 0.77 Waste fuel and boiler cleaning solution 2516 4 oil - other 2008 0.062 0.641 Waste fuel 2516 4 oil - other 2009 0.06 0.696 Waste fuel 2516 4 oil - residual or bunker 2007 2.613 34.36 2516 4 oil - residual or bunker 2008 2.604 34.324 2516 4 oil - residual or bunker 2009 1.37 21.389 2517 3 natural gas 2007 94.17 45 2517 3 natural gas 2008 97.7 68.3 2517 3 natural gas 2009 98.2 73.7 2517 3 oil - other 2007 0 0 No other fuel utilized 2517 3 oil - other 2008 0 0 No other fuel utilized 2517 3 oil - other 2009 0.02 0 Boiler cleaning solution 2517 3 oil - residual or bunker 2007 5.83 55 2517 3 oil - residual or bunker 2008 2.3 31.7 2517 3 oil - residual or bunker 2009 1.78 26.3 2517 4 natural gas 2007 96.5 58.5 2517 4 natural gas 2008 98.7 78.9 2517 4 natural gas 2009 97.19 64.04 2517 4 oil - other 2007 0 0 No other fuel utilized 2517 4 oil - other 2008 0 0 No other fuel utilized 2517 4 oil - other 2009 0.04 0 Boiler cleaning solution Page 24boiler_fuels

2517 4 oil - residual or bunker 2007 3.5 41.5 2517 4 oil - residual or bunker 2008 1.3 21.1 2517 4 oil - residual or bunker 2009 2.77 35.96

Page 25boiler_fuels

Waste fuel and boiler cleaning solutions Waste fuel and boiler cleaning solution

Waste fuel and boiler cleaning solution Waste fuel and boiler cleaning solution

Waste fuel and boiler cleaning solution

Waste fuel and boiler cleaning solution

Page 26boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 2516 1 Overfire Air 9/1/1992 2516 2 Overfire Air 9/1/1994 2516 3 Advanced Overfire Air 3/1/2010 2516 3 Overfire Air 4/1/1994 2516 4 Overfire Air 4/1/1993 2517 3 Overfire Air 4/1/1994 2517 4 Overfire Air 4/1/1995

Page 27boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 2516 1 Low Sulfur Fuel Oil 1/1/1988 2516 2 Low Sulfur Fuel Oil 1/1/1988 2516 3 Low Sulfur Fuel Oil 1/1/1988 2516 4 Low Sulfur Fuel Oil 1/1/1988 2517 3 Low Sulfur Fuel Oil 1/1/1988 2517 4 Low Sulfur Fuel Oil 1/1/1988

Page 28boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 29facility _units facility _id unit_id 2516 1 2516 2 2516 3 2516 4 2517 3 2517 4

Page 30unit_boilers

facility _id unit_id boiler_id 2516 1 1 2516 2 2 2516 3 3 2516 4 4 2517 3 3 2517 4 4

Page 31facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 2516 PM1 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 12/1/1972 2516 PM2 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 4/1/1974 2516 PM3 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 6/1/1972 2516 PM4 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 12/1/1977 2517 PM3 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 11/1/1958 2517 PM4 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 11/1/1960

Page 32facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 33facility _sampling_ports facility _id sampling_port_id 2516 SP1N 2516 SP1S 2516 SP2N 2516 SP2S 2516 SP3N 2516 SP3S 2516 SP4N 2516 SP4S 2517 SP3E 2517 SP3W 2517 SP4

Page 34facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 2516 Stack1 600 16.75 84 2516 Stack2 600 16.75 84 2516 Stack3 600 16.75 84 2516 Stack4 600 16.75 84 2517 Stack3 425 10.25 118 2517 Stack4 425 10.25 118

Page 35configurations

facility _id configuration_id 2516 Unit1 2516 Unit2 2516 Unit3 2516 Unit4 2517 Unit3 2517 Unit4

Page 36configuration_components

facility _id configuration_id

component_id

order component_type port_near 2516 Unit1 1 1 Unit 2516 Unit1 PM1 2 PM control 2516 Unit1 SP1N 3 Sam pling Port pevious 2516 Unit1 SP1S 3 Sam pling Port pevious 2516 Unit1 Stack1 4 Stack 2516 Unit2 2 1 Unit 2516 Unit2 PM2 2 PM control 2516 Unit2 SP2N 3 Sam pling Port pevious 2516 Unit2 SP2S 3 Sam pling Port pevious 2516 Unit2 Stack2 4 Stack 2516 Unit3 3 1 Unit 2516 Unit3 PM3 2 PM control 2516 Unit3 SP3N 3 Sam pling Port pevious 2516 Unit3 SP3S 3 Sam pling Port pevious 2516 Unit3 Stack3 4 Stack 2516 Unit4 4 1 Unit 2516 Unit4 PM4 2 PM control 2516 Unit4 SP4N 3 Sam pling Port pevious 2516 Unit4 SP4S 3 Sam pling Port pevious 2516 Unit4 Stack4 4 Stack 2517 Unit3 3 1 Unit 2517 Unit3 PM3 2 PM control 2517 Unit3 SP3E 3 Sam pling Port pevious 2517 Unit3 SP3W 3 Sam pling Port pevious 2517 Unit3 Stack3 4 Stack 2517 Unit4 4 1 Unit 2517 Unit4 PM4 2 PM control 2517 Unit4 SP4 3 Sam pling Port next 2517 Unit4 Stack4 4 Stack

Page 37configuration_pollutants1

facility _id configuration_id

pollutant_name

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 2516 Unit1 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

2 hours 2516 Unit2 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

2 hours 2516 Unit2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1 percent by

weight Continuous 2516 Unit1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1 percent by

weight Continuous 2516 Unit3 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

2 hours 2516 Unit3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1 percent by

weight Continuous 2516 Unit4 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

2 hours 2516 Unit4 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.75 percent by

weight Continuous 2516 Unit4 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.3 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.2 pound per million British Thermal Unit (lb/MMBtu) 2517 Unit3 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

2 hours 2517 Unit3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1 percent by

weight Continuous 2517 Unit4 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

2 hours 2517 Unit4 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1 percent by

weight Continuous

Page 38configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method Method 5 Method 5 SO2 is limited by

the percent sulfur in the fuel oil SO2 is limited by

the percent sulfur in the fuel oil Method 5 SO2 is limited by

the percent sulfur in the fuel oil Method 5 SO2 is controlled by

the percent sulfur in the fuel oil 3 hours Lim its apply to oil and gas firing, respectively Method 5 SO2 is controlled by

the sulfur content of the fuel Method 5 SO2 is controlled by

the sulfur content of the fuel

Page 39configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting No There are no guarentees associated with this parameter Once during the term of the permit

Five years Sem i annually No There are no guarentees associated with this parameter Once during the term of the permit

Five years Sem i-Annually 1 percent by

weight No All fuel purchased on specification. Source tank to be verified in compliance with limit. Five years Annually 1 percent by

weight No All fuel is purchased on specification. Source tank to be verified in compliance with the limit Five years Annually No There are no guarentees associated with this parameter Once during the term of the permit

Five years Sem i annually 1 percent by

weight No All fuel is purchased on specification. Source tank to be verified in compliance with limit Five years Annual No There are no guarentees associated with this parameter Once during the term of the permit

Five years Sem i Annual 0.75 percent by

weight No All fuel is purchased on specification. Source tank to be verified in compliance with the limit Five years Annual Lim its apply

to oil and gas firing, respectively No There are no guarentees associated with this parameter Continuous Five years Quarterly No There is no guarentee associated with this parameter Once during the term of the permit

Five years Sem i-Annual 1 percent by

weight No Fuel oil is purchased on specification. Source tank to be verified in compliance with the limit Five years Annual No Once during the term of the permit Five years Sem i-Annual 1 percent by

weight No Fuel oil is purchased on specification. Source tank to be verified in compliance with the limit Five years Annual

Page 40control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 41control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 42control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 43control_technologies feed_rate_units

Page 44control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 45control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_name

Page 46control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investment

total_operating_costs

base_year

Page 47control_costs

CBI

Page 48misc_controls

facility _id misc_control_id

control_description

Page 49misc_control_configurations

facility _id misc_control_id

configuration_id

Page 50fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county 2516 S08095 1/1/2009 95880.7 barrels oil 2516 S08096 1/1/2009 105056.1 barrels oil 2516 S08098 1/1/2009 89805.56 barrels oil 2516 S09001 1/1/2009 110596.6 barrels oil 2516 S09002 1/1/2009 120485.6 barrels oil 2516 S09003 1/1/2009 120884.9 barrels oil 2516 S09004 1/1/2009 110133.8 barrels oil 2516 S09006 1/1/2009 110207 barrels oil 2516 S09007 1/1/2009 107708 barrels oil 2516 S09022 1/1/2009 108247.3 barrels oil 2516 S09023 1/1/2009 108114.5 barrels oil 2516 S09025 2/1/2009 108559 barrels oil 2516 S09026 2/1/2009 106254.2 barrels oil 2516 S09031 2/1/2009 99658.65 barrels oil 2516 S09051 7/1/2009 120490.1 barrels oil 2516 S09074 12/1/2009 110317.3 barrels oil 2516 S09078 12/1/2009 108240.5 barrels oil 2517 S09005 1/1/2009 84618.49 barrels oil 2517 S09021 1/1/2009 83697.25 barrels oil 2517 S09029 2/1/2009 72852.67 barrels oil 2517 S09056 8/1/2009 99701.76 barrels oil

Page 51fuel_shipments

coal_seam shipment_method

Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge Barge

Page 52fuel_shipment_configurations

facility _id shipment_id

configuration_id 2516 S08095 Unit1 2516 S08095 Unit2 2516 S08095 Unit3 2516 S08095 Unit4 2516 S08096 Unit1 2516 S08096 Unit2 2516 S08096 Unit3 2516 S08096 Unit4 2516 S08098 Unit1 2516 S08098 Unit2 2516 S08098 Unit3 2516 S08098 Unit4 2516 S09001 Unit1 2516 S09001 Unit2 2516 S09001 Unit3 2516 S09001 Unit4 2516 S09002 Unit1 2516 S09002 Unit2 2516 S09002 Unit3 2516 S09002 Unit4 2516 S09003 Unit1 2516 S09003 Unit2 2516 S09003 Unit3 2516 S09003 Unit4 2516 S09004 Unit1 2516 S09004 Unit2 2516 S09004 Unit3 2516 S09004 Unit4 2516 S09006 Unit1 2516 S09006 Unit2 2516 S09006 Unit3 2516 S09006 Unit4 2516 S09007 Unit1 2516 S09007 Unit2 2516 S09007 Unit3 2516 S09007 Unit4 2516 S09022 Unit1 2516 S09022 Unit2 2516 S09022 Unit3 2516 S09022 Unit4 2516 S09023 Unit1 2516 S09023 Unit2 2516 S09023 Unit3 2516 S09023 Unit4 2516 S09025 Unit1 2516 S09025 Unit2 2516 S09025 Unit3 2516 S09025 Unit4 2516 S09026 Unit1 2516 S09026 Unit2 2516 S09026 Unit3 Page 53fuel_shipment_configurations

2516 S09026 Unit4 2516 S09031 Unit1 2516 S09031 Unit2 2516 S09031 Unit3 2516 S09031 Unit4 2516 S09051 Unit1 2516 S09051 Unit2 2516 S09051 Unit3 2516 S09051 Unit4 2516 S09074 Unit1 2516 S09074 Unit2 2516 S09074 Unit3 2516 S09074 Unit4 2516 S09078 Unit1 2516 S09078 Unit2 2516 S09078 Unit3 2516 S09078 Unit4 2517 S09005 Unit3 2517 S09005 Unit4 2517 S09021 Unit3 2517 S09021 Unit4 2517 S09029 Unit3 2517 S09029 Unit4 2517 S09056 Unit3 2517 S09056 Unit4

Page 54fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 55fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 56fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies

Page 57fuel_shipment_samples analysis_copies

Page 58fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 59test_reports

facility _id report_id report_typeother_type report_description report_begin_date

report_end_date

before_control

during_deviation 2516 Unit # 2 PM

compliance Particulate Matter testing 5/1/2008 Yes No 2516 Unit #3 PM Test

compliance Compliance test for Particulate Matter 6/19/2008 Yes No

Page 60test_reports

deviation_reports No Yes

Page 61test_report_configurations

facility _id report_id configuration_id 2516 Unit # 2 PMUnit2 2516 Unit #3 PM Test

Unit3

Page 62test_report_fuels

facility _id report_id fuel_id 2516 Unit # 2 PM

#6 Fuel Oil 2516 Unit #3 PM Test

#6 Fuel Oil

Page 63test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 2516 Unit # 2 PM

#6 Fuel Oil oil - residual or bunker 100 100 2516 Unit #3 PM Test

#6 Fuel Oil natural gas 1.7 1.7 2516 Unit #3 PM Test

#6 Fuel Oil oil - residual or bunker 98.3 98.3

Page 64cem_data

facility _id time_period

cem_period_description 2516 NA

Page 65cem_data_pollutants1

facility _id time_period

pollutant_name

Page 66test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent

Page 67test_report_sampling

fg_fraction

Page 68sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content

Page 69sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature

Page 70sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value

Page 71sampling_runs

fuel_sulfur

Page 72sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_name conc conc_units conc_ND conc_MDL

Page 73sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment

Page 74sampling_run_pollutants1 run_pollutant_comment

Page 75sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 76sampling_run_fuel fuel_conc_MDL

Page 77