# Search Help 

# More Search Options

Printable Version



# Fluorescent Lamp Ballasts

Test Procedure Notice of

Proposed Rulemaking Public

Meeting

The Department of Ener gy (DOE) is holding a

public meeting that will first cover the test

procedure notice of proposed rulemaking

(NOPR) for fluorescent lamp ballasts and then

the energy conservation standards rulemaking

for the same products. This public meeting

gives DOE an opportunity to present the

proposals in the test procedure NOPR and to

respond to stakeholder questions. DOE will

also seek input from interested parties on the

planned methodologies, assumptions, data

sources, and the NEMA Alternative Test

Procedure Handout.

The following documents are available as

Adobe Acrobat PDFs. Download Adobe

Reader

.



# Meeting Materials

z 

# Test Procedures for Fluorescent Lamp

Ballasts; NOPR, as issued by the

Secretary of Energy ( PDF 2.0 MB )

NOTE: The official version of the NOPR

will be published in the Federal Register

shortly.

z 

# NEMA Alternative Test Procedure EERE Information Center

Programs and Offices



# DATE: April 26, 2010

TIME: 9:00 a.m. ET

LOCATION:

U.S. Department of Energy

Forrestal Building

Room 8E-089

1000 Independence Avenue, SW

Washington, DC 20585 

# Pa g e 1 of 3 A pp liances and Commercial E q ui p ment Standards: Fluorescent Lam p Ballasts Test Proce...

3/23/2010 htt p ://www1.eere.ener gy

. g ov/buildin g s/a pp liance

_ standards/residential/fluorescent

_ lam p_

...

# Handout ( PDF 90 KB )

This document outlines a draft NEMA

test procedure for the measurement

of fluorescent lamp ballast efficiency.

DOE summarizes this test procedure

as an alternative method under

consideration in th e fluorescent lamp

ballast active mode test procedure

NOPR in section III.E.2. DOE requests

comment on this alternative test

method as noted in section V.E.5 of

the test procedure NOPR.

z 

# Test Data, Appendix 5c of the

fluorescent lamp ballast energy

conservation standard preliminary

technical support document ( PDF 234

KB )

z 

# Presentation (available after meeting)

z 

# Agenda (available after meeting)

z 

# Transcript (availabl e after meeting)

A transcript will also be available for

public inspection in the Building

Technologies Program Reading Room,

between 9:00 a.m. and 4:00 p.m.,

Monday through Friday, except

Federal holidays. To schedule an

appointment or to purchase this

transcript, contact:

Brenda Edwards

U.S. Department of Energy

Building Technologies Program

950 L'Enfant Plaza, 6th Floor

Washington, DC 20024

202-586-2945



# How to Submit Comments

Submit comments electronically, by mail, or

by courier. Wherever possible, comments in

the electronic format should carry the

electronic signature of the author. Absent an

electronic signature, comments submitted

electronically must be authenticated by

submitting the signed original paper

document.

All comments submitted must identify the

docket number, and regulatory identifier

number (RIN).

z 

# Docket Number EERE-2009-BT-TP0016 and RIN 1904-AB99

.

Comments may be submitted using any of

the following methods: 

# Pa g e 2 of 3 A pp liances and Commercial E q ui p ment Standards: Fluorescent Lam p Ballasts Test Proce...

3/23/2010 htt p ://www1.eere.ener gy

. g ov/buildin g s/a pp liance

_ standards/residential/fluorescent

_ lam p_

...

# Building Technologies Program Home | EERE Home | U.S. Department of Energy

Webmaster | Web Site Policies | Security & Privacy | USA.gov

Content Last Updated: 03/19/2010 z 

# Federal eRulemaking Portal:

http://www.regulations.gov/

Follow the instructions for submitting

comments.

z 

# E-mail:

FLB

- 2009

- TP

- 0016@ee.doe

Include docket number EERE-2009-

BT-TP-0016 and/or RIN 1904-AB99 in

the subject line of the message.

z 

# Postal Mail:

Brenda Edwards

U.S. Department of Energy

Building Technologies Program

Mailstop EE-2J

1000 Independence Avenue, SW

Washington, DC 20585-0121

Please include one signed original

paper copy.

z 

# Hand Delivery or Courier:

Brenda Edwards

U.S. Department of Energy

Building Technologies Program

950 L'Enfant Plaza, 6th Floor

Washington, DC 20024

Telephone: 202-586-2945

Please include one signed original

paper copy.

Comments should clearly identify

docket number EERE-2009-BT-TP0016.



# Contact Information

Linda Graves

Project Manager

202-586-1851

Printable Version 

# Pa g e 3 of 3 A pp liances and Commercial E q ui p ment Standards: Fluorescent Lam p Ballasts Test Proce...

3/23/2010 htt p ://www1.eere.ener gy

. g ov/buildin g s/a pp liance

_ standards/residential/fluorescent

_ lam p_

...

# 5C-i APPENDIX 5C. FLUORESCENT LAMP BALLAST TEST DATA

TABLE OF CONTENTS

5C.1 INTRODUCTION .........................................................................................................5C-1

5C.2 TEST DATA..................................................................................................................5C-1

LIST OF TABLES

Table 5C.1 Ballasts That Operate Four-F oot MBP and Two-Foot U-Shaped Lam ps ...............5C-1

Table 5C.2 Ballasts That Operate Four-Foot MiniBP T5 SO Lamps ........................................5C-5

Table 5C.3 Ballasts That Operate Four-Foot MiniBP T5 HO Lamps .......................................5C-5

Table 5C.4 Ballasts That Operate Eight-Foot SP Slimline Lamps ............................................5C-6

Table 5C.5 Ballasts That Oper ate Eight-Foot RDC HO Lamps ................................................5C-7

Table 5C.6 Ballasts That Operate Four-Foot MBP and Two-Foot U-Shaped Lamps in the

Residential Sector ........................................................................................5C-7

Table 5C.7 Ballasts that Operate Eight- Foot HO Lamps in Cold Temperature

Applications and Outdoor Signs ..................................................................5C-85C-1APPENDIX 5C.FLUORESCENT LAMP BALLAST TEST DATA5C.1INTRODUCTIONThe following appendix lists the test data DOE used to develop the engineering analysis. DOEchose to test a variety ofballasts from many different manufacturers. Through an independenttesting facility, DOE tested both the ballast efficacy factor (BEF)and ballast efficiency (BE) of the ballast. For BEF, DOE usedthe test procedure outlined in 10 CFR 430, Subpart B, Appendix Q.ForBE, DOE used the test procedure proposedin the fluorescent lamp ballastactive mode test procedure notice of proposed rulemaking.Three examples of each ballast type were tested, and the average of the three test results is displayed for each ballast type in the tablesbelow.5C.2TEST DATATable 5C.1 Ballasts That Operate Four-Foot MBP and Two-Foot U-Shaped LampsManufacturerNumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) in BEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallast InputVoltage (V)in BE testingMeasuredBallastInputPower(W) inBEtestingMeasuredLampArcPower(W) inBEtestingMeasuredBallastEfficiencyA1T84832IS120N120.0333.40.8892.658120.0334.728.30.814B1T84832IS120N120.0330.60.8422.747120.0430.525.20.827A1T84832IS277Y277.1032.20.8772.722277.1032.927.10.823A1T84832IS277Y277.1029.70.8492.855277.0829.424.90.845A1T84832IS277N277.1732.30.8822.736277.0832.726.50.812B1T84832IS277N277.1031.50.8632.743277.0631.325.50.814B1T84832IS277Y277.1028.00.8483.026277.0824.321.70.892B1T84832IS277Y277.1027.80.8433.036277.1323.921.30.891C1T84832IS277Y277.1030.20.8852.929277.1031.827.60.869C1T84832IS277Y277.0730.00.8552.852277.0830.325.70.848D1T84832IS277N277.1031.10.8892.859277.0531.826.90.8455C-2Manufacturer NumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) in BEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallast InputVoltage (V)in BE testingMeasuredBallastInputPower(W) inBEtestingMeasuredLampArcPower(W) inBEtestingMeasuredBallastEfficiencyD1T84832IS277Y277.1029.80.8432.833277.0329.024.00.828D1T84832IS277Y277.1030.80.8662.814277.0630.925.60.830D1T84832PS277Y277.0732.60.9252.838277.0733.828.40.840A2T124834RS277N276.9763.50.8621.359N.D.N.D.N.D.N.D.B2T124834RS277Y276.9964.30.8551.330N.D.N.D.N.D.N.D.C2T124834RS277N276.9163.40.8621.361N.D.N.D.N.D.N.D.D2T124834RS277N276.9861.20.8411.374N.D.N.D.N.D.N.D.D2T124834RS277N277.0165.30.8521.305N.D.N.D.N.D.N.D.A2T84832IS277Y277.0753.30.7951.492277.0748.542.20.870A2T84832IS277Y277.0257.90.8801.519277.0861.155.00.900A2T84832IS277Y277.0078.01.1561.482277.14115.3105.40.914A2T84832IS277Y277.0750.80.7631.503277.1844.839.30.876A2T84832IS277Y277.0356.00.8601.535277.0957.552.00.905A2T84832IS277N277.0078.91.1851.502276.99122.5113.00.923A2T84832IS277N277.0460.40.8751.450****B2T84832IS277N277.0758.20.8461.454277.0957.549.40.860B2T84832IS277Y277.0078.61.1991.524277.0879.874.10.928B2T84832IS277Y277.0349.50.7581.531277.2039.235.10.895B2T84832IS277Y277.0654.10.8421.554277.0748.344.30.918B2T84832IS277Y277.0078.41.1561.475277.02116.4106.00.911B2T84832IS277Y277.0750.00.7601.520277.1143.738.10.871B2T84832IS277Y276.9856.40.8661.535277.0458.953.50.908C2T84832IS277Y277.0079.01.1791.493276.94125.3115.50.921C2T84832IS277Y277.0750.00.7581.515277.0144.239.40.890C2T84832IS277Y277.0256.40.8741.549276.9659.354.60.920C2T84832IS277Y276.9780.31.1921.485277.01126.4115.70.915C2T84832IS277Y277.0754.20.7661.413277.0647.438.50.811C2T84832IS277Y277.0555.90.8631.544276.9957.953.10.917D2T84832IS277N277.0748.50.7461.538277.1141.637.30.897D2T84832IS277N277.0352.10.8141.563277.0750.045.80.916D2T84832IS277N277.0753.50.7811.460277.0549.141.80.852D2T84832IS277N277.0259.00.8641.466277.0160.752.30.861D2T84832IS277Y277.0349.80.7521.508277.0743.137.50.8695C-3Manufacturer NumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) in BEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallast InputVoltage (V)in BE testingMeasuredBallastInputPower(W) inBEtestingMeasuredLampArcPower(W) inBEtestingMeasuredBallastEfficiencyD2T84832IS277Y277.0355.40.8401.516277.0454.848.80.890D2T84832IS277Y277.0075.51.1151.476277.02108.399.30.916D2T84832IS277Y277.0055.60.8551.538277.0056.851.50.907A2T84832PS277Y277.0746.00.6831.483277.0535.229.80.846A2T84832PS277Y276.9556.70.8611.517277.0355.550.00.902A2T84832PS277N276.9863.50.8961.412277.0469.258.30.843B2T84832PS277N277.0058.30.8791.509277.0361.555.10.896B2T84832PS277Y277.0076.61.1331.479276.99110.5101.80.921B2T84832PS277Y277.0048.30.7151.483277.0640.434.40.851B2T84832PS277Y277.0758.60.8711.486277.0361.454.70.891B2T84832PS277Y277.0745.80.6091.331277.0434.424.10.701C2T84832PS277Y276.9856.90.8631.516276.9758.953.10.902D2T84832PS277Y277.0063.30.8911.408277.0562.451.60.827A3T84832IS277Y276.8785.30.8691.019277.1388.079.70.906A3T84832IS277Y277.0083.20.8461.017277.1582.574.10.898A3T84832IS277N277.0085.90.8721.015277.0989.680.70.900B3T84832IS277N277.0083.90.8441.006277.1983.474.60.895B3T84832IS277Y276.9782.50.8501.031277.0981.774.20.907B3T84832IS277Y276.9784.80.8541.008277.0485.776.20.890C3T84832IS277Y276.9785.00.8681.022277.1587.879.80.909C3T84832IS277YN.D.N.D.N.D.N.D.277.0087.079.50.913D3T84832IS277N277.0379.40.8261.040277.1077.871.60.920D3T84832IS277N277.0087.60.8450.964277.0788.275.60.857D3T84832IS277Y277.0083.10.8481.021277.0784.976.90.905D3T84832IS277Y277.0082.70.8441.021277.0982.874.40.900D3T84832PS277Y277.0090.80.8610.949277.1288.375.00.849A4T84832IS277Y276.93100.50.7760.772277.1389.679.60.888A4T84832IS277Y276.85112.80.8520.756276.87114.3104.70.916A4T84832IS277Y276.90155.61.1910.766277.02237.6211.70.891A4T84832IS277Y276.9795.30.7450.782277.1480.772.10.894A4T84832IS277Y276.92114.40.8660.757276.90118.1108.60.920A4T84832IS277N276.86115.50.8730.756276.86120.5110.90.920B4T84832IS277N277.01111.50.8370.751277.21110.299.70.9055C-4Manufacturer NumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) in BEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallast InputVoltage (V)in BE testingMeasuredBallastInputPower(W) inBEtestingMeasuredLampArcPower(W) inBEtestingMeasuredBallastEfficiencyB4T84832IS277Y276.90143.61.1360.791277.05176.0166.50.946B4T84832IS277Y276.9796.40.7500.777277.1383.674.60.892B4T84832IS277Y276.95110.10.8390.762276.92107.899.30.921B4T84832IS277Y276.90147.41.1420.775 B4T84832IS277Y276.93110.60.8580.776277.10112.1101.10.902B4T84832IS277YN.D.N.D.N.D.N.D.277.0486.277.60.900C4T84832IS277Y276.93145.21.1240.774** **C4T84832IS277Y276.9797.90.7710.788277.1488.180.90.918C4T84832IS277Y276.91113.70.8610.758276.97117.1107.80.921C4T84832IS277Y276.9796.00.7530.785277.1682.874.20.897C4T84832IS277Y276.94112.60.8720.774276.94115.0106.10.923D4T84832IS277N276.9793.30.7360.789277.1478.671.70.911D4T84832IS277N276.93106.80.8230.771276.87103.696.40.931D4T84832IS277N276.90147.71.1370.770277.12205.1190.50.929D4T84832IS277N277.0096.80.7470.772277.1583.774.80.894D4T84832IS277N276.86110.90.8420.760276.85111.2102.10.918D4T84832IS277Y276.9393.40.7370.788277.1579.972.30.905D4T84832IS277Y276.90109.20.8310.761276.88108.099.00.917D4T84832IS277Y276.97109.50.8530.779277.15111.3101.20.909B4T84832PS120N120.04117.00.8670.742120.12122.0110.50.906A4T84832PS277Y277.0392.10.7120.772277.1271.064.30.907A4T84832PS277Y276.88114.60.8880.775276.91110.1102.60.932A4T84832PS277N276.90120.30.8650.719276.85130.1109.10.839B4T84832PS277Y276.90148.81.1470.771277.03224.2207.40.925B4T84832PS277Y276.97112.70.8770.778276.87119.8110.80.925C4T84832PS277Y276.83116.10.8800.758276.9195.785.50.894D4T84832PS277Y276.91118.80.8430.709276.88112.694.60.840B6T84832IS277YN.D.N.D.N.D.N.D.277.03283.3267.30.943N.D. indicates DOE did not perform the measurement, “no data.”* When connected to a resistor, the ballast did notoperate. The ballast did operate a lamp successfully.5C-5Table 5C.2 Ballasts That OperateFour-Foot MiniBP T5 SO LampsManufacturerNumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) in BEtestingMeasuredLamp ArcPower(W) in BEtestingMeasuredBallastEfficiencyC1T54628PS277Y277.2330.80.9973.234277.0932.928.80.873A2T54628PS277Y277.1164.91.0191.570277.1467.158.40.871B2T54628PS277Y277.0459.80.9571.600277.1758.251.10.877B2T54628PS277Y276.9870.51.1411.618277.1589.481.10.907C2T54628PS277Y277.0663.61.0101.587277.1567.058.50.874C2T54628PS277Y276.8761.71.0001.620277.0818.39.60.525D2T54628PS277Y277.0558.70.9481.613276.8962.554.40.869D2T54628PS277Y276.9365.41.0611.624276.6968.161.00.896Table 5C.3 Ballasts That Operate Four-Foot MiniBP T5 HO LampsManufacturerNumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) in BEFtestingMeasuredBallastInputPower (W)in BEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower (W)in BEtestingMeasuredLamp ArcPower (W)in BEtestingMeasuredBallastEfficiencyC1T54654PS277Y276.8959.21.0161.716277.0659.553.50.899A2T54654PS277Y277.13126.31.0170.806277.05111.497.80.878B2T54654PS277Y277.07124.80.9880.791****B2T54654PS277Y276.97120.70.9700.804276.99108.696.90.892C2T54654PS277Y276.94123.71.0060.813277.05105.393.90.891D2T54654PS277Y277.04122.41.0150.829277.05103.493.40.903A4T54654PS277Y277.03240.91.0510.436276.99228.4207.60.909B4T54654PS277Y277.07220.70.9750.442276.99211.9189.50.894D4T54654PS277Y277.03226.51.0130.447277.02207.7187.50.903* When connected to a resistor, the ballast did notoperate. The ballast did operate a lamp successfully.5C-6Table 5C.4 Ballasts That OperateEight-Foot SP Slimline LampsManufacturerNumberof LampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) inBEtestingMeasuredLampArcPower(W) inBEtestingMeasuredBallastEfficiencyB1T89659IS277Y277.0756.00.8941.596276.9649.045.30.926B1T89659IS277Y277.0757.60.8781.523277.0153.747.30.882D1T89659IS277N277.0057.70.8831.529277.1954.948.60.884D2T129660IS120N119.92107.40.8500.792N.D.N.D.N.D.N.D.A2T129660IS277N277.00114.30.9070.794N.D.N.D.N.D.N.D.B2T129660IS277Y276.89111.90.8920.798N.D.N.D.N.D.N.D.C2T129660IS277N277.00114.80.9080.791N.D.N.D.N.D.N.D.D2T129660IS277N276.83111.10.8850.797N.D.N.D.N.D.N.D.D2T129660IS277N276.86109.50.8840.807N.D.N.D.N.D.N.D.D2T129660IS277Y276.88111.20.9000.809N.D.N.D.N.D.N.D.A2T89659IS120N120.51104.50.8290.794120.1189.481.20.908B2T89659IS120N120.20112.90.8760.776120.10102.291.70.898A2T89659IS277Y277.03105.70.8500.804277.1492.884.80.914A2T89659IS277N277.00105.40.8510.807277.1492.284.40.915B2T89659IS277N277.00107.50.8590.799277.1697.589.60.920B2T89659IS277Y276.91105.20.8590.817277.0691.884.90.925B2T89659IS277YN.D.N.D.N.D.N.D.277.1298.290.70.924C2T89659IS277Y276.94109.50.8870.810277.0999.892.10.922C2T89659IS277Y276.97141.51.1260.796277.01176.1164.30.933C2T89659IS277Y277.0093.50.7580.811276.9471.965.80.914C2T89659IS277Y276.77108.00.8740.810277.0397.089.40.922D2T89659IS277N276.86104.90.8680.827277.1694.488.50.938D2T89659IS277N277.0092.80.7580.817277.1772.166.90.928D2T89659IS277N276.97110.20.8730.792277.14102.192.50.906D2T89659IS277N276.93147.11.1560.786277.07184.3169.10.917D2T89659IS277Y276.92109.70.8660.789277.1599.889.80.900N.D. indicates DOE did not perform the measurement, “no data.”5C-7Table 5C.5 Ballasts That Operate Eight-Foot RDC HO LampsManufacturerNumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) in BEtestingMeasuredLamp ArcPower(W) in BEtestingMeasuredBallastEfficiencyA2T129695RS277Y276.90188.30.8580.456N.D.N.D.N.D.N.D.A2T129695RS277N276.91166.00.8440.509N.D.N.D.N.D.N.D.B2T129695RS277N276.87196.70.8790.447N.D.N.D.N.D.N.D.C2T129695RS277N276.75208.40.9170.440N.D.N.D.N.D.N.D.C2T129695RS277N276.92164.60.8360.508N.D.N.D.N.D.N.D.D2T129695RS277N276.84172.20.8750.508N.D.N.D.N.D.N.D.D2T129695RS277Y276.81169.10.8970.531N.D.N.D.N.D.N.D.D2T129695RS277N276.92195.00.9010.462N.D.N.D.N.D.N.D.D2T89686IS120N120.03138.80.6220.448120.08108.296.10.888B2T89686IS277Y277.07138.70.6520.470277.1197.386.50.889D2T89686IS277N277.03142.80.6760.473277.16102.791.80.894A2T89686PS277Y276.93185.80.8640.465277.03197.2172.60.875C2T89686PS277Y277.10175.00.7730.442277.08165.7148.40.896A2T89686RS120N120.00162.10.7400.456120.02134.9113.40.841N.D. indicates DOE did not perform the measurement, “no data.”Table 5C.6 Ballasts That Operate Four-Foot MBP and Two-Foot U-Shaped Lamps inthe Residential SectorManufacturerNumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) in BEtestingMeasuredLamp ArcPower(W) in BEtestingMeasuredBallastEfficiencyA1T124834RS120N119.9534.00.6651.957N.D.N.D.N.D.N.D.A2T124834RS120N120.0063.10.8411.332N.D.N.D.N.D.N.D.B2T124834RS120N119.9764.60.8601.332N.D.N.D.N.D.N.D.K2T124834RS120N120.1842.40.6271.480N.D.N.D.N.D.N.D.L2T124834RS120N120.1050.30.6521.297N.D.N.D.N.D.N.D.E2T84832IS120N119.8855.30.8321.505120.0454.348.10.885E2T84832IS120N120.0253.10.7801.470120.0548.842.20.864A2T84832IS120N120.0054.80.8311.517119.9953.348.20.904B2T84832IS120N120.0055.70.8181.470119.9852.946.40.8775C-8Manufacturer NumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) in BEtestingMeasuredLamp ArcPower(W) in BEtestingMeasuredBallastEfficiencyC2T84832IS120N120.0057.50.8571.490119.9656.850.20.885D2T84832IS120N120.0055.90.8391.500119.9855.349.40.893A4T84832IS120N120.10102.10.7830.767120.1792.482.40.891B4T84832IS120N120.10107.20.8210.766120.15102.491.80.897C4T84832IS120N120.10113.20.8560.756120.11112.7100.10.888D4T84832IS120N120.10114.60.8450.738120.05113.298.60.871N.D. indicates DOE did not perform the measurement, “no data.”Table 5C.7 Ballasts that Operate Eight-Foot HO Lampsin Cold Temperature Applications and Outdoor SignsManufacturerNumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) in BEtestingMeasuredLamp ArcPower(W) in BEtestingMeasuredBallastEfficiencyF1T1296110IS120N120.10103.90.9010.867N.D.N.D.N.D.N.D.F2T1296110IS120N120.03174.40.7900.453N.D.N.D.N.D.N.D.D2T1296110IS120Y120.00133.40.6130.460N.D.N.D.N.D.N.D.F3T1296110IS120N120.10175.10.5370.306N.D.N.D.N.D.N.D.G3T1296110IS120N120.13177.10.5420.306N.D.N.D.N.D.N.D.F4T1296110IS120N120.10269.10.6030.224N.D.N.D.N.D.N.D.H4T1296110IS120N119.90260.80.6180.237N.D.N.D.N.D.N.D.G4T1296110IS120N120.10269.70.6070.225N.D.N.D.N.D.N.D.D4T1296110IS120Y120.00254.60.6070.238N.D.N.D.N.D.N.D.D4T1296110IS120Y119.90264.00.6280.238N.D.N.D.N.D.N.D.F4T1296110RS120N120.03388.40.7780.200N.D.N.D.N.D.N.D.I4T1296110RS120N120.03180.00.3040.169N.D.N.D.N.D.N.D.D4T1296110RS120N120.00393.60.7710.196N.D.N.D.N.D.N.D.F6T1296110IS120N119.73340.30.5310.156N.D.N.D.N.D.N.D.F6T1296110IS120N120.23408.80.6360.156N.D.N.D.N.D.N.D.H6T1296110IS120N120.03397.80.6250.157N.D.N.D.N.D.N.D.G6T1296110IS120N120.00349.30.6090.174N.D.N.D.N.D.N.D.G6T1296110IS120N119.90343.80.5460.159N.D.N.D.N.D.N.D.5C-9Manufacturer NumberofLampsLampDiameter(1/8 ofinches)LampLength(inches)LampNominalPower(W)StartingMethodBallastNominalInputVoltage(V)UniversalInputVoltage?(Y/N)MeasuredBallastInputVoltage(V) inBEFtestingMeasuredBallastInputPower(W) inBEFtestingMeasuredBallastFactor inBEFtestingMeasuredBallastEfficacyFactorMeasuredBallastInputVoltage(V) in BEtestingMeasuredBallastInputPower(W) in BEtestingMeasuredLamp ArcPower(W) in BEtestingMeasuredBallastEfficiencyD6T1296110IS120Y120.00399.20.6410.161N.D.N.D.N.D.N.D.J6T1296110IS120Y120.10418.50.6290.150N.D.N.D.N.D.N.D.N.D. indicates DOE did not perform the measurement, “no data.”