Project: Statoil OCS Permitting Project

Control Option: Developer Emergency Generator (E GEN) Engine Equipped with SCRDate: July 23, 2012Author: Kyle Heitkamp Pa

Economic Factors

Equipment Life (n) Worst case based on longest period of time Statoil would lease the drilling vessel 

Annual Interest Rate (I) OAQPS 

Design Parameters

SCR NOx Removal Efficiency (SCR NOx) Based on vendor estimate. 

Direct Costs (DC) Total Equip + ST + Fr + Install + Electric 

Total Purchased Equipment Cost (Total Equip) Equip + SCR Ancillary Equipment + CEMS + F&S + Pipe + Insul + Paint SCR Equipment Cost (Equip) SCR Cost Estimate SCR Ancilliary Equipment Conservatively assume no additional Equipment 

NOx CEMS (CEMS) Conservatively assume no CEMS Sales Tax (ST) Conservatively assume no sales tax Freight (Fr) 0.05 * Total Equip 

Foundations and Support (F&S) 0.10 * Equip 

Total Purchased Equipment Installation (Install) Electrical (Electric) 0.08 * Equip 

Piping (Pipe) Insulation for Ductwork (Insul) Painting (Paint) 

Indirect Costs (IC) CE + E&S + Contract + SU + Test 

Construction Expenses (CE) 0.08 * DC Engineering and Supervision (E&S) 0.08 * DC Contractor Fees (Contract) 0.05 * DC 

Start-up (SU) Assume no downtime to install SCR on emergency generator 

Initial Compliance Certification/CEMS Certification Emissions Test (Test) Conservatively assume no testing 

Project Contingency (PC) 0.15 * (DC + IC) 

Total Plant Cost (B) DC + IC + PC 

Total Capital Investment (TCI) B 

DESIGN CONDITIONS

TOTAL CAPITAL INVESTMENT

0.35 * Total Equip (NOTE that no cost for removal has been included even though such a cost would be expected)
Project: Statoil OCS Permitting Project

Control Option: Developer Emergency Generator (E GEN) Engine Equipped with SCRDate: July 23, 2012Author: Kyle Heitkamp Pa

Annual Maintenance Cost (AMC) 0.015 * TCI 

Annual Reagent Cost (ARC) assume zero for worst case 

Annual Catalyst Replace Cost (ACRC) assume zero for worst case Annual Electricity Cost (AEC) assume zero for worst case Annual CEMS Required QA/QC Cost (CEMS QAQC) Conservative assumption 

Direct Annual Costs (DAC) AMC + ARC + ACRC + AEC + CEMS QAQC Capital Recovery Factor (CRF) (i * (1 + i)^n) / ((1 + i)^n - 1) 

Fuel Penalty (FP) assume zero for worst case 

Taxes/Insurance/Admin (TIA) Indirect Annual Costs (IDAC) (CRF * TCI) + FP + TIA 

Total Annual Costs (TAC) DAC + IDAC NOx Removal due to the Installation of SCR Unit Difference in emissions between 9.2 and 0.9 g/kW-hr emission factor. 

Cost Effectiveness of SCR Unit TAC / NOx Removal 

COST EFFECTIVENESS

TOTAL ANNUAL COSTS
Project: Statoil OCS Permitting Project

Control Option: Developer Main Engines Equipped with SCRDate: July 20, 2012Author: Kyle Heitkamp Pa

Economic Factors

Equipment Life (n) Worst case based on longest period of time Statoil would lease the drilling vessel 

Annual Interest Rate (I) OAQPS 

Design Parameters

SCR NOx Removal Efficiency (SCR NOx) Calculated using the difference in emissions between 8.2 and 2.0 g/kW-hr emission factor. 

Direct Costs (DC) Total Equip + Instr + ST + Fr + Install + Electric 

Total Purchased Equipment Cost (Total Equip) Equip + F&S + Pipe + Insul + Paint 

SCR Equipment Cost (Equip) per discussions with Wartsila Instrumentation (Instr)Sales Tax (ST) Freight (Fr) 0.25 * Equip (assume 25% since equipment would come from Europe) 

Foundations and Support (F&S)Total Purchased Equipment Installation (Install) Estimate for SCR equipment installation and removal 

Electrical (Electric) included with Installation Costs 

Piping (Pipe) included with Installation Costs Insulation for Ductwork (Insul) included with Installation Costs Painting (Paint) included with Installation Costs 

Indirect Costs (IC) CE + E&S + Contract + SU + Test 

Construction Expenses (CE) Conservatively assume no CE

Engineering and Supervision (E&S) Conservatively assume no E&SContractor Fees (Contract) Conservatively assume no Contractor FeesStart-up (SU) Estimate based on four days for SCR install and removal per engine ($500,000/day) 

Initial Compliance Certification/CEMS Certification Emissions Test (Test) Conservatively assume no testing

Project Contingency (PC) Conservatively assume no contingencyTotal Plant Cost (B) DC + IC + PC 

Total Capital Investment (TCI) B 

DESIGN CONDITIONS

TOTAL CAPITAL INVESTMENT
Project: Statoil OCS Permitting Project

Control Option: Developer Main Engines Equipped with SCRDate: July 20, 2012Author: Kyle Heitkamp Pa

Annual Maintenance Cost (AMC) included with DAC belowAnnual Reagent Cost (ARC) included with DAC belowAnnual Catalyst Replace Cost (ACRC) included with DAC belowAnnual Electricity Cost (AEC) included with DAC belowAnnual CEMS Required QA/QC Cost (CEMS QAQC) included with DAC belowDirect Annual Costs (DAC) Capital Recovery Factor (CRF) (i * (1 + i)^n) / ((1 + i)^n - 1) 

Fuel Penalty (FP) Conservatively assume no fuel penalty for electric heater required prior to SCR

Taxes/Insurance/Admin (TIA) 0.04 * TCI use 0.005 * DC to exclude rig time expense, property taxes, and minimal admin 

Indirect Annual Costs (IDAC) (CRF * TCI) + FP + TIA 

Total Annual Costs (TAC) DAC + IDAC NOx Removal due to the Installation of SCR Unit Difference in emissions between 8.2 and 2.0 g/kW-hr emission factor. 

Cost Effectiveness of SCR Unit TAC / NOx Removal 

COST EFFECTIVENESS - TYPICAL CASE

TOTAL ANNUAL COSTS

[per Wartsila quote (includes maintenance and consumables) $8.82/MWh (assume per SCR/engine)]
Project: Statoil OCS Permitting Project

Control Option: Developer Emergency Generator Engine (E GEN) ReplacementDate: August 17, 2012

Author: Kyle Heitkamp Page 

Economic Factors

Equipment Life (n) Worst case based on longest period of time Statoil would lease the drilling vessel 

Annual Interest Rate (I) OAQPS 

Design Parameters

NOx Removal Efficiency Calculated using the difference in emissions between 9.2 and 5.8 g/kW-hr emission factor. 

Direct Costs (DC) Total Equip + Fr + Install 

Total Purchased Equipment Cost (Total Equip) Equipment Cost (Equip) (Very conservative estimate on new Tier 3 engine cost) Instrumentation (Instr) Sales Tax (ST) Freight (Fr) 0.05 * Equip 

Foundations and Support (F&S) Total Purchased Equipment Installation (Install) 0.05 * Equip (Estimate to remove the existing engine and install the new engine) Electrical (Electric) Piping (Pipe) Insulation for Ductwork (Insul) Painting (Paint) 

Indirect Costs (IC) CE + E&S + Contract + SU + Test 

Construction Expenses (CE) Engineering and Supervision (E&S) Contractor Fees (Contract) Start-up (SU) Conservatively set to $0 

Initial Compliance Certification Emissions Test (Test) Conservatively set to $0 

Project Contingency (PC) 0.15 * (DC + IC) 

Total Plant Cost (B) DC + IC + PC Total Capital Investment (TCI) B 

DESIGN CONDITIONS

TOTAL CAPITAL INVESTMENT
Project: Statoil OCS Permitting Project

Control Option: Developer Emergency Generator Engine (E GEN) ReplacementDate: August 17, 2012

Author: Kyle Heitkamp Page 

Annual Maintenance Cost (AMC) Annual Reagent Cost (ARC) Annual Catalyst Replace Cost (ACRC) Annual Electricity Cost (AEC) Direct Annual Costs (DAC) Capital Recovery Factor (CRF) (i * (1 + i)^n) / ((1 + i)^n - 1) 

Fuel Penalty (FP) Taxes/Insurance/Admin (TIA) Indirect Annual Costs (IDAC) (CRF * TCI) + FP + TIA 

Total Annual Costs (TAC) DAC + IDAC NOx Removal Difference in emissions between 9.2 (baseline) and 5.8 (Tier 3) g/kW-hr emission factors. 

Cost Effectiveness TAC / NOx Removal 

COST EFFECTIVENESS - WORST CASE

TOTAL ANNUAL COSTS
Project: Statoil OCS Permitting Project

Control Option: Discoverer Americas Emergency Generator (E GEN) Engine Equipped with SCRDate: July 23, 2012Author: Kyle Heitkamp Pa

Economic Factors

Equipment Life (n) Worst case based on longest period of time Statoil would lease the drilling vessel 

Annual Interest Rate (I) OAQPS 

Design Parameters

SCR NOx Removal Efficiency (SCR NOx) Based on vendor estimate. 

Direct Costs (DC) Total Equip + ST + Fr + Install + Electric 

Total Purchased Equipment Cost (Total Equip) Equip + SCR Ancillary Equipment + CEMS + F&S + Pipe + Insul + Paint SCR Equipment Cost (Equip) SCR Cost Estimate SCR Ancilliary Equipment Conservatively assume no additional Equipment 

NOx CEMS (CEMS) Conservatively assume no CEMS Sales Tax (ST) Conservatively assume no sales tax Freight (Fr) 0.05 * Total Equip 

Foundations and Support (F&S) 0.10 * Equip 

Total Purchased Equipment Installation (Install) Electrical (Electric) 0.08 * Equip 

Piping (Pipe) Insulation for Ductwork (Insul) Painting (Paint) 

Indirect Costs (IC) CE + E&S + Contract + SU + Test 

Construction Expenses (CE) 0.08 * DC Engineering and Supervision (E&S) 0.08 * DC Contractor Fees (Contract) 0.05 * DC 

Start-up (SU) Assume no downtime to install SCR on emergency generator 

Initial Compliance Certification/CEMS Certification Emissions Test (Test) Conservatively assume no testing 

Project Contingency (PC) 0.15 * (DC + IC) 

Total Plant Cost (B) DC + IC + PC 

Total Capital Investment (TCI) B 

DESIGN CONDITIONS

TOTAL CAPITAL INVESTMENT

0.35 * Total Equip (NOTE that no cost for removal has been included even though such a cost would be expected)
Project: Statoil OCS Permitting Project

Control Option: Discoverer Americas Emergency Generator (E GEN) Engine Equipped with SCRDate: July 23, 2012Author: Kyle Heitkamp Pa

Annual Maintenance Cost (AMC) 0.015 * TCI 

Annual Reagent Cost (ARC) assume zero for worst case 

Annual Catalyst Replace Cost (ACRC) assume zero for worst case Annual Electricity Cost (AEC) assume zero for worst case Annual CEMS Required QA/QC Cost (CEMS QAQC) Conservative assumption 

Direct Annual Costs (DAC) AMC + ARC + ACRC + AEC + CEMS QAQC Capital Recovery Factor (CRF) (i * (1 + i)^n) / ((1 + i)^n - 1) 

Fuel Penalty (FP) assume zero for worst case 

Taxes/Insurance/Admin (TIA) Indirect Annual Costs (IDAC) (CRF * TCI) + FP + TIA 

Total Annual Costs (TAC) DAC + IDAC NOx Removal due to the Installation of SCR Unit Difference in emissions between 9.8 and 1.0 g/kW-hr emission factor. 

Cost Effectiveness of SCR Unit TAC / NOx Removal 

COST EFFECTIVENESS

TOTAL ANNUAL COSTS
Project: Statoil OCS Permitting Project

Control Option: Discoverer Americas Main Engines ReplacementDate: August 16, 2012Author: Kyle Heitkamp Pa

Economic Factors

Equipment Life (n) Worst case based on longest period of time statoil would lease the drilling vessel 

Annual Interest Rate (I) OAQPS 

Design Parameters

NOx Removal Efficiency Calculated using the difference in emissions between12.07 and 9.7 g/kW-hr emission factor. 

Direct Costs (DC) 

Total Purchased Equipment Cost (Total Equip) Equipment Cost (Equip) Instrumentation (Instr) Sales Tax (ST) Freight (Fr) Foundations and Support (F&S) Total Purchased Equipment Installation (Install) Electrical (Electric) Piping (Pipe) Insulation for Ductwork (Insul) Painting (Paint) 

Indirect Costs (IC) CE + E&S + Contract + SU 

Construction Expenses (CE) Engineering and Supervision (E&S) Contractor Fees (Contract) Start-up (SU) Estimate for downtime related to engine replacement Project Contingency (PC) Total Plant Cost (B) DC + IC + PC Total Capital Investment (TCI) B 

DESIGN CONDITIONS

TOTAL CAPITAL INVESTMENT
Project: Statoil OCS Permitting Project

Control Option: Discoverer Americas Main Engines ReplacementDate: August 16, 2012Author: Kyle Heitkamp Pa

Annual Maintenance Cost (AMC) Annual Reagent Cost (ARC) Annual Catalyst Replace Cost (ACRC) Annual Electricity Cost (AEC) Direct Annual Costs (DAC) Capital Recovery Factor (CRF) (i * (1 + i)^n) / ((1 + i)^n - 1) 

Fuel Penalty (FP) Taxes/Insurance/Admin (TIA) Indirect Annual Costs (IDAC) (CRF * TCI) + FP + TIA Total Annual Costs (TAC) DAC + IDAC NOx Removal Difference in emissions between12.07 and 9.7 g/kW-hr emission factor. 

Cost Effectiveness TAC / NOx Removal 

COST EFFECTIVENESS

TOTAL ANNUAL COSTS

EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.110, LARGE IC ENGINES >500 HP, 

FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 2, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONTR

SC-0113 2/8/2012 5/9/2012 PYRAMAX CERAMICS, LLC EMERGENCY GENERATORS 1 - 8 17.110 DIESEL 757 HP 4 GR/KW-H BACT- PSD ENGINES MU

COMPLY WIT

FL-0328 10/27/2011 4/5/2012 ENI - HOLY CROSS DRILLING PROJECT MAIN PROPULSION ENGINES 17.110 DIESEL 12.7 G/KW-H BACT- PSD

GOOD COMBU

ADDITIONA

PRACTICE STA

ENGINE PERFO

SYSTEM AND 

WITH TURB

MEASU

FL-0328 10/27/2011 4/5/2012 ENI - HOLY CROSS DRILLING PROJECT CRANE ENGINES (UNITS 1 AND 2) 17.110 DIESEL 9.5 TONS PER YEAR BACT- PSD CERTIFIED EP

GOOD COM

FL-0328 10/27/2011 4/5/2012 ENI - HOLY CROSS DRILLING PROJECT CRANE ENGINES (UNITS 3 AND 4) 17.110 DIESEL 9.7 TONS PER YEAR BACT- PSD GOOD COM

FL-0328 10/27/2011 4/5/2012 ENI - HOLY CROSS DRILLING PROJECT EMERGENCY ENGINE 17.110 DIESEL 0.4 TONS PER YEAR BACT- PSD GOOD COM

FL-0328 10/27/2011 4/5/2012 ENI - HOLY CROSS DRILLING PROJECT EMERGENCY FIRE PUMP ENGINE 17.110 DIESEL 0.02 TONS PER YEAR BACT- PSD GOOD COM

AK-0072 7/14/2011 11/18/2011 DUTCH HARBOR POWER PLANT EU 15 CATERPILLAR C-280-16 17.110

ULTRA LOW 

SULFUR 

DISTILLATE

4400 KW 9.8 G/KW-H BACT- PSD ENGINE HAS 

AFTER COOLER 

T

FL-0327 6/13/2011 2/3/2012 ANADARKO - PHEONIX PROSPECT MAIN PROPULSION ENGINES 17.110 DIESEL 12.7 G/KW-HR BACT- PSD

GOOD C

MAINTENANC

MANAGEME

CONCENTR

SYSTEM AS D

PERM

FL-0327 6/13/2011 2/3/2012 ANADARKO - PHEONIX PROSPECT EMERGENCY ENGINE 17.110 DIESEL 9.4 TONS PER PROJECT BACT- PSD LIMITED USE O

RECORDKEE

LA-0251 4/26/2011 12/12/2011 FLOPAM INC. FACILITY LARGE GENERATOR ENGINES (17 UNITS) 17.110 DIESEL 6.32 LB/H LAER 

FL-0322 12/23/2010 7/6/2011 SWEET SORGHUM-TO-ETHANOL ADVANCED BIOREFINERY EMERGENCY GENERATORS, TWO 2682 HP EA 17.110 ULTRA LOW SULFUR DISTILLATE 6.4 G/KW-H BACT- PSD 

SD-0005 6/29/2010 10/14/2010 DEER CREEK STATION EMERGENCY GENERATOR 17.110 DISTILLATE OIL 2000 KW BACT- PSD 

SD-0005 6/29/2010 10/14/2011 DEER CREEK STATION FIRE WATER PUMP 17.110 DISTILLATE OIL 577 HP BACT- PSD 

NV-0050 11/30/2009 3/15/2010 MGM MIRAGE EMERGENCY GENERATORS - UNITS LX024 AND LX025 AT LUXOR 17.110 DIESEL OIL 2206 HP 0.0131 LB/HP-H Other Case-by- Case TURBOCHARG

AND LEAN-

NV-0049 8/20/2009 12/1/2009 HARRAH'S OPERATING COMPANY, INC LARGE INTERNAL COMBUSTION ENGINES (>600 HP) - UNIT HA13 17.110 DIESEL OIL 1232 HP 0.024 LB/HP-H BACT- PSD THE UNIT I

TUR

ID-0018 6/25/2009 10/5/2010 LANGLEY GULCH POWER PLANT EMERGENCY GENERATOR ENGINE 17.110 DIESEL 750 KW 6.4 G/KW-H BACT- PSD TIER 2 ENG

COMBUS

LA-0231 6/22/2009 5/17/2010 LAKE CHARLES GASIFICATION FACILITY EMERGENCY DIESEL POWER GENERATOR ENGINES (2) 17.110 DIESEL 1341 hp each 17.09 LB/H BACT- PSD COMPLY WITH 4

LA-0231 6/22/2009 5/17/2010 LAKE CHARLES GASIFICATION FACILITY FIRE WATER DIESEL PUMPS (3) 17.110 DIESEL 575 HP each 6.02 LBS/HR BACT- PSD COMPLY WITH 4

AK-0066 6/15/2009 8/6/2009 ENDICOTT PRODUCTION FACILITY, LIBERTY DEVELOPMENT PROJECT EU ID 58, CAMP ENGINE 3 17.110 DISTILLATE 1041 HP 4.7 G/HP-H BACT- PSD GOOD COMBUS

LA-0204 2/27/2009 8/6/2009 PLAQUEMINE PVC PLANT LARGE EMERGENCY ENGINES 17.110 DIESEL 3.2 LB/MMBTU BACT- PSD GOOD COMBUS

GASEOUS FUEL 

NH-0015 2/27/2009 10/5/2010 CONCORD STEAM CORPORATION EMRGENCY GENERATOR 1 17.110 DIESEL FUEL 5.6 MMBtu/hr 1.98 LB/MMBTU LAER LESS THAN 500 

PER CONSECUT

NH-0015 2/27/2009 10/5/2010 CONCORD STEAM CORPORATION EMERGENCY GENERATOR 2 17.110 DIESEL FUEL 11.6 MMBtu/hr 1.98 LB/MMBTU LAER OPERATES LES

CONSECUTIVE 

ID-0017 2/10/2009 2/5/2010 POWER COUNTY ADVANCED ENERGY CENTER 2 MW EMERGENCY GENERATOR, SCR25 17.110 ASTM #1, 2, DIESEL 2000 KW BACT- PSD GOOD COMBUS

CERTIFIED PER 

ID-0017 2/10/2009 2/5/2010 POWER COUNTY ADVANCED ENERGY CENTER 500 KW EMERGENCY GENERATOR, FIRE PUMP, SRC26 17.110 ASTM #1, 2, DIESEL 500 KW BACT- PSD GOOD COMBUS

CERTIFICATION 

OK-0129 1/23/2009 2/18/2010 CHOUTEAU POWER PLANT EMERGENCY DIESEL GENERATOR (2200 HP) 17.110 LOW SULFUR DIESEL 2200 HP 23.15 LB/H BACT- PSD 

FL-0310 1/12/2009 1/26/2010 SHADY HILLS GENERATING STATION 2.5 MW EMERGENCY GENERATOR 17.110 ULTRA LOW SULFUR OIL 2.5 MW 6.9 G/HP-H BACT- PSD PURCHASE MO

STRINGENT AS UNDER EPA CE

THRUPUT EMISSIONS LIMIT

Page 1 of 6
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.110, LARGE IC ENGINES >500 HP, 

FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 2, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONTR

THRUPUT EMISSIONS LIMIT

OH-0317 11/20/2008 2/20/2009 OHIO RIVER CLEAN FUELS, LLC EMERGENCY GENERATOR 17.110 DIESEL FUEL OIL 2922 HP 26.47 LB/H BACT- PSD

GOOD COMBUSENGINE DESIGNRETARD, TURBTEMPERATURE 

IA-0095 9/19/2008 1/30/2009 TATE & LYLE INDGREDIENTS AMERICAS, INC. EMERGENCY GENERATOR 17.110 DIESEL 700 KW 6.2 G/KW-H BACT- PSD 

IA-0095 9/19/2008 1/30/2009 TATE & LYLE INDGREDIENTS AMERICAS, INC. FIRE PUMP ENGINE 17.110 DIESEL 575 HP 3.9 G/KW-H BACT- PSD 

NJ-0073 3/8/2008 8/12/2008 TRIGEN DUAL FUEL ENGINES ON 100 % DISTILLATE FUEL OIL 17.110 DISTILLATE FUEL OIL 1 MMGAL/Y R 12 G/B-HP-H RACT 

NV-0047 2/26/2008 10/21/2008 NELLIS AIR FORCE BASE LARGE INTERNAL COMBUSTION ENGINES (>500 HP) 17.110 DIESEL OIL 7.58 G/B-HP-H BACT- PSD TURBOCHARGE

MD-0037 1/28/2008 12/27/2010 MEDIMMUNE FREDERICK CAMPUS

TWO (2) DIESEL (NO. 2 FUEL OIL) FIRED, NON-EMERGENCY GENERATORS EACH RATED AT 2500 KILOWATTS (3604 BRAKE HORSEPOWER)

17.110 DIESEL (NO. 2 FUEL OIL) 2500 KW 0.61 G/HP-H LAER SELECTIVE CAT

(SCR) SYSTEM 

MD-0037 1/28/2008 12/27/2010 MEDIMMUNE FREDERICK CAMPUS

THREE (3) DIESEL (NO. 2 FUEL OIL) FIRED, EMERGENCY GENERATORS EACH RATED AT 2500 KILOWATTS (3604 BRAKE HORSEPOWER)

17.110 DIESEL (NO. 2 FUEL OIL) 2500 KW 6.06 G/HP-H LAER 

VA-0305 9/26/2007 7/28/2008 INGENCO K&O FACILITY ELECTRIC GENERATION 17.110 DISTILLATE OIL 550 HHP 240 T/YR N/A CHARGE AIR CO

GOOD COMBUS

LA-0219 8/15/2007 4/22/2008 CREOLE TRAIL LNG IMPORT TERMINAL FIREWATER PUMP DIESEL ENGINE 17.110 DIESEL 660 HP 10.07 LB/H BACT- PSD

GOOD COMBUSGOOD ENGINE INCORPORATINTIMING RETARD

LA-0219 8/15/2007 4/22/2008 CREOLE TRAIL LNG IMPORT TERMINAL FIREWATER PUMP DIESEL ENGINE 17.110 DIESEL 525 HP 6.74 LB/H BACT- PSD

GOOD COMBUSGOOD ENGINE INCORPORATINTIMING RETARD

LA-0219 8/15/2007 4/22/2008 CREOLE TRAIL LNG IMPORT TERMINAL DIESEL EMERGENCY GENERATOR NOS. 1 & 2 17.110 DIESEL 2168 HP EA. 37.95 LB/H BACT- PSD

GOOD COMBUSGOOD ENGINE INCORPORATINTIMING RETARD

IA-0088 6/29/2007 10/9/2007 ADM CORN PROCESSING - CEDAR RAPIDS EMERGENCY GENERATOR 17.110 DIESEL 1500 KW 4.5 G/BHP-H BACT- PSD

NO SPECIFIC CIS SPECIFED. EMEET LIMITS ES(TIER 2 NONROREQUIRE ANY NTECHNOLOGIES REQ. TO MEET 

IA-0088 6/29/2007 10/9/2007 ADM CORN PROCESSING - CEDAR RAPIDS FIRE PUMP 17.110 DIESEL #2 540 HP 2.8 G/BHP-H BACT- PSD

NO SPECIFIC CIS SPECIFED. EMEET LIMITS ES(TIER 3 NONROREQUIRE ANY NTECHNOLOGIES REQ. TO MEET 

MS-0086 5/8/2007 3/4/2010 CHEVRON PRODUCTS COMPANY, PASCAGOULA REFINERY TEMPORARY, PORTABLE CRUDE I GENERATOR 17.110 DIESEL 1.3 LB/H BACT- PSD SELECTIVE CAT

(SCR) 

PA-0271 2/23/2007 8/5/2010 MERCK & CO. WESTPOINT MOBILE EMERGENCY GENERATOR 17.110 DIESEL 6.8 GR/BHP-H

Other 

Case-byCase 

AK-0064 1/31/2007 2/13/2009 DUTCH HARBOR POWER PLANT I.C. 17.110 FUEL OIL 5711 KW 13.6 G/KW-H BACT- PSD FUEL INJECTIO

AND AFTERCOODESIGN) 

AK-0064 1/31/2007 12/27/2010 DUTCH HARBOR POWER PLANT I.C. 17.110 FUEL OIL 5000 KW 1.36 G/KW-H BACT- PSD REDUCE NOX B

AK-0064 1/31/2007 2/13/2009 DUTCH HARBOR POWER PLANT I.C. 17.110 FUEL OIL 5000 KW 1.36 G/KW-H BACT- PSD 

LA-0211 12/27/2006 7/16/2008 GARYVILLE REFINERY EMERGENCY GENERATORS (DOCK & TANK FARM) (21-08 & 22-08) 17.110 DIESEL 0.031 LB/HP-H BACT- PSD USE OF DIESEL 

CONTENT OF 15 

NV-0045 12/11/2006 3/31/2008 SLOAN QUARRY LARGE INTERNAL COMBUSTION ENGINE 17.110 DIESEL OIL 12 GAL/H 0.058 LB/T BACT- PSD N/A 

KS-0028 10/18/2005 3/9/2006 NEARMAN CREEK POWER STATION EMERGENCY BLACK START GENERATOR 17.110 NO. 2 FUEL OIL 24.1 MMBTU/H 84.8 LB/H BACT- PSD

EMERGENCY DHAVE NOT BEEADDITIONAL NOOF INTERMITTE

Page 2 of 6
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.110, LARGE IC ENGINES >500 HP, 

FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 2, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONTR

THRUPUT EMISSIONS LIMIT

AZ-0046 4/14/2005 8/25/2006 ARIZONA CLEAN FUELS YUMA FIRE WATER PUMPS NOS 1 AND 2 17.110 NO. 2 DIESEL FUEL 5.46 MMBTU/H 4 G/KW-H BACT- PSD 

AZ-0046 4/14/2005 8/25/2006 ARIZONA CLEAN FUELS YUMA EMERGENCY GENERATOR 17.110 NO. 2 DIESEL FUEL 10.9 MMBTU/H 6.4 G/KW-H BACT- PSD 

IA-0076 3/23/2005 4/22/2008 JOHN DEERE PRODUCT ENGINEERING CENTER TEST CELL 17.110 DIESEL 24.5 GAL/H 1.52 LB/MMBTU BACT- PSD GOOD COMBUS

WA-0329 2/11/2005 7/5/2006 DARRINGTON ENERGY COGENERATION POWER PLANT STANDBY GENERATOR 17.110 DIESEL FUEL 1 MW BACT- PSD ENGINE MUST B

FEDERAL STAN

WA-0328 1/11/2005 8/14/2007 BP CHERRY POINT COGENERATION PROJECT EMERGENCY GENERATOR 17.110 DIESEL FUEL 1.5 MW BACT- PSD

THE ENGINE MUSATISFY THE FESTANDARDS OF OF PURCHASE.

LA-0194 11/24/2004 9/3/2009 SABINE PASS LNG TERMINAL FIREWATER PUMP DIESEL ENGINES 1-3 17.110 DIESEL 660 HP EACH 12.2 LB/H BACT- PSD GOOD ENGINE 

OPERATING PR

LA-0194 11/24/2004 9/3/2009 SABINE PASS LNG TERMINAL STANDBY GENERATOR DIESEL ENGINES 1-2 17.110 DIESEL 2220 HP EACH BACT- PSD COMPLYING WI

IIII 

NC-0112 11/23/2004 8/14/2007 NUCOR STEEL

DIESEL FIRED EMERGENCY GENERATORS AND DIESEL FIRED EMERGENCY WATER PUMPS

17.110 FUEL OIL BACT- PSD

OPERATION LIMOPERATION FOGENERATOR ANMONTH PERIOD

AK-0061 11/5/2004 7/23/2007 SNAKE RIVER POWER PLANT WARTSILA 12V32B DIESEL ELECTRIC GENERATOR 17.110 DIESEL FUEL 5211 kW 134 LB/H BACT- PSD

1. FUEL INJECT(THREE DEGRESEPARATE LOW COOLING WATECOOLER (LT SE

PA-0244 10/20/2004 3/10/2005 FIRST QUALITY TISSUE, LLC FIRE PUMP 17.110 #2 FUEL OIL 575 hp 0.031 LB/HP-H BACT- PSD 

OH-0275 8/24/2004 8/31/2006 PSI ENERGY-MADISON STATION EMERGENCY DIESEL GENERATOR, 2 17.110 DIESEL FUEL 17.21 MMBTU/H 55.07 LB/H BACT- PSD 

WV-0023 3/2/2004 2/3/2009 MAIDSVILLE EMERGENCY GENERATOR 17.110 DIESEL 1801 HP 20.9 LB/H BACT- PSD GOOD COMBUS

WI-0207 1/21/2004 8/16/2005 ACE ETHANOL - STANLEY IC ENGINE, DIESEL GENERATOR SET, B70 17.110 1850 BHP 13 G/B-HP-H BACT- PSD LIMIT ON HOUR

HRS/MO, 12 MO

MN-0054 12/4/2003 8/24/2006 MANKATO ENERGY CENTER INTERNAL COMBUSTION ENGINE, LARGE 17.110 DIESEL FUEL 1850 HP 12.7 G/B-HP-H BACT- PSD GOOD COMBUS

AK-0060 10/10/2003 6/3/2005 DUTCH HARBOR SEAFOOD PROCESSING FACILITY IC ENGINE, GENERATOR, FUEL OIL, (3) 17.110 DISTILLATE FUEL OIL 2220 KW 42.3 LB/H BACT- PSD WATER INJECT

AK-0059 9/29/2003 5/22/2009 USAF EARECKSON AIR STATION IC ENGINE, DIESEL, (2) 17.110 DIESEL 3000 KW 9.7 LB/H BACT- PSD SCR 

AK-0059 9/29/2003 5/22/2009 USAF EARECKSON AIR STATION IC ENGINES 17.110 DIESEL BACT- PSD GOOD COMBUS

NC-0105 8/21/2003 1/11/2006 UNIVERSITY OF NORTH CAROLINA - CHAPEL HILL EMERGENCY GENERATORS 17.110 DIESEL N/A BACT DOES NO

EDUCATIONAL 

OH-0254 8/14/2003 7/5/2005 DUKE ENERGY WASHINGTON COUNTY LLC EMERGENCY DIESEL-FIRED GENERATOR 17.110 DIESEL 600 KW 12.4 LB/H BACT- PSD LOW SULFUR F

CONTROL 

VA-0276 6/20/2003 2/20/2004 INGENCO - CHARLES CITY PLANT IC ENGINES, (48) 17.110 FUEL OIL 550 HP 2.4 LB/MMBTU N/A

AIR TO FUEL RATURBOCHARGICOOLING SYSTRATIO SHALL BSEPARATE ENGFOR EACH ENG

IA-0067 6/17/2003 2/26/2009 MIDAMERICAN ENERGY COMPANY EMERGENCY GENERATOR 17.110 DIESEL FUEL 97.73 GAL/H 1.71 LB/MMBTU BACT- PSD GOOD COMBUS

OK-0090 3/21/2003 10/10/2003 DUKE ENERGY STEPHENS, LLC STEPHENS ENERGY IC ENGINE, BACKUP GENERATOR, DIESEL 17.110 DIESEL 749 BHP 2.16 LB/MMBTU BACT- PSD ENGINE DESIGN 

OF OPERATION 

OK-0091 3/18/2003 10/10/2003 CARDINAL FG CO./ CARDINAL GLASS PLANT IC ENGINES, EMERGENCY GENERATORS (2) 17.110 DIESEL 2000 KW 2.035 LB/MMBTU BACT- PSD ENGINE DESIGN 

OF OPERATION 

CA-0988 2/1/2003 9/4/2003 PACIFIC BELL IC ENGINES 17.110 DIESEL FUEL 2935 HP 6.9 G/B-HP-H LAER NC-0074 1/24/2003 3/12/2004 BRIDGESTONE/FIRESTONE NORTH AMERICAN TIRE IC ENGINES, AIR COMPRESSORS, DIESEL, (5) 17.110 DIESEL 4.46 MMBTU/H 7.8 LB/H BACT- PSD IGNITION TIMIN

TX-0407 12/6/2002 10/26/2004 STERNE ELECTRIC GENERATING FACILITY EMERGENCY GENERATOR 17.110 DIESEL 1350 HP 41.9 LB/H BACT- PSD 

PA-0209 11/8/2002 8/16/2006 ORCHARD PARK GENERATING STATION IC ENGINE, GENERATOR 17.110 FUEL OIL 8086 BHP 1.5 G/BHP-H Other Case-by- Case LEAN BURN, SC

COMBUSTION C

IA-0061 9/25/2002 5/6/2004 CITY OF PELLA IC ENGINES, DIESEL, (14) 17.110 DIESEL 144 G/H 1.71 LB/MMBTU

Other 

Case-byCase COMBUSTION A

Page 3 of 6
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.110, LARGE IC ENGINES >500 HP, 

FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 2, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONTR

THRUPUT EMISSIONS LIMIT

OH-0266 8/15/2002 4/29/2008 UNIVERSITY OF CINCINNATI DIESEL FIRED ENGINES (2), 2 MW, 2922 BHP 17.110 DIESEL FUEL OIL 19.17 MMBTU/H 40.92 LB/H BACT- PSD 

OK-0070 6/13/2002 5/12/2004 GENOVA OK I POWER PROJECT DIESEL ENGINE, BACKUP GENERATOR 17.110 DIESEL 750 KW 3.01 LB/MMBTU BACT- PSD ENGINE DESIGN 

HOURS 

SC-0064 5/23/2002 1/13/2003 SCE&G - JASPER COUNTY GENERATING FACILITY GENERATOR, EMERGENCY,DIESEL FUEL 17.110 DIESEL 2000 KW 59.5 LB/H BACT- PSD 

NM-0049 5/20/2002 3/10/2005 PHELPS DODGE TYRONE, INC IC ENGINES, NON-DUAL FUEL MODE, (15) 17.110 FUEL OIL 3090 HP/H 31.4 LB/H

Other 

Case-byCase GOOD OPERAT

OK-0072 5/6/2002 7/7/2003 REDBUD POWER PLT DIESEL ENGINE, EMERGENCY GENERATOR 17.110 DIESEL FUEL 1818 HP 0.024 LB/B-HP-H BACT- PSD 

IA-0058 4/10/2002 6/21/2004 GREATER DES MOINES ENERGY CENTER EMERGENCY GENERATOR 17.110 DIESEL 700 KW 22.69 LB/H BACT- PSD RETARDED ING

DEGREES) 

AR-0051 4/1/2002 5/6/2004 DUKE ENERGY-JACKSON FACILITY GENERATOR, DIESEL-FIRED 17.110 DIESEL FUEL 671 HP 14 G/B-HP-H BACT- PSD GOOD OPERAT

NJ-0036 10/24/2001 7/8/2008 AES RED OAK LLC EMERGENCY GENERATOR 17.110 DIESEL FUEL 49 MMBTU/H 159.65 LB/H LAER LIMITED USE NC-0075 8/20/2001 3/12/2004 FORT BRAGG IC ENGINES, DIESEL, (17) 17.110 DIESEL 44.4 T/YR BACT- PSD EACH GENERAT

SHAVING MODE MORE THAN 25

LA-0122 8/14/2001 3/17/2005 MANSFIELD MILL CATERPILLAR BACK-UP DIESEL AIR COMPRESSORS, 2 17.110 DIESEL FUEL 775 HP EACH 38.6 LB/H BACT- PSD PREVENTATIVE 

LA-0122 8/14/2001 3/17/2005 MANSFIELD MILL AUXILIARY DIESEL GENERATORS NO.1 & NO.2 17.110 DIESEL FUEL 1100 HP EACH 34 LB/H BACT- PSD PREVENTATIVE 

LA-0122 8/14/2001 3/17/2005 MANSFIELD MILL ADMINISTRATION BUILDING DIESEL GENERATOR 17.110 DIESEL 587 HP 18.1 LB/H BACT- PSD PREVENTATIVE 

CA-1010 7/11/2001 10/27/2005

POWER SYSTEM ASSOCIATES/JOHNSON POWER SYSTEMS

IC ENGINE, EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 764 BHP 6.19 G/BHP-H BACT- PSD TURBOCHARGE 

CA-1012 7/11/2001 10/28/2005

POWER SYSTEM ASSOCIATES/JOHNSON POWER SYSTEMS

IC ENGINES, EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 685 BHP 4.17 G/BHP-H BACT- PSD TURBOCHARGE

CA-1013 7/11/2001 10/28/2005

POWER SYSTEM ASSOCIATES/JOHNSON POWER SYSTEMS

IC ENGINE, EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 610 BHP 4.17 G/BHP-H BACT- PSD TURBOCHARGE

CA-1014 7/11/2001 10/28/2005

POWER SYSTEM ASSOCIATES/JOHNSON POWER SYSTEMS

IC ENGINE, EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 536 BHP 4.8 G/BHP-H BACT- PSD TURBOCHARGE

OH-0255 3/29/2001 5/12/2008 AEP WATERFORD ENERGY LLC EMERGENCY GENERATOR 17.110 DIESEL 1000 KW 0.82 T/YR BACT- PSD 

AR-0040 12/29/2000 6/30/2003 DUKE ENERGY HOT SPRINGS GENERATORS, (2) DIESEL 17.110 #2 FUEL OIL 600 KW 14 G/B-HP-H BACT- PSD CLEAN FUEL, C

TX-0401 12/15/2000 8/30/2004 COTTONWOOD ENERGY PROJECT FIRE WATER PUMP 17.110 10.39 LB/H BACT- PSD 

TX-0401 12/15/2000 8/30/2004 COTTONWOOD ENERGY PROJECT EMERGENCY DIESEL GENERATOR 17.110 12.4 LB/H BACT- PSD 

WI-0174 9/20/2000 12/3/2002 BADGER GENERATING CO LLC DIESEL ENGINE, GENERATOR (4) 17.110 DIESEL 3.5 MMBTU/H 15.44 LB/H BACT- PSD GOOD COMBUS

PERMIT LIMITS H. 

WI-0174 9/20/2000 12/3/2002 BADGER GENERATING CO LLC DIESEL ENGINE, EMERGENCY FIRE PUMP 17.110 DIESEL 3.8 MMBTU/H 16.76 LB/H BACT- PSD

GOOD COMBUSEQUIPMENT USLIMITS IN LB/H, H 

VT-0014 9/5/2000 12/16/2002 OKEMO MOUNTAIN INC. GENERATOR, FUEL OIL 17.110 NO 2 FUEL OIL 1480 BHP 1.6 G/B-HP-H RACT SCR TX-0384 8/23/2000 10/26/2004 BRAZOS VALLEY ELECTRIC GENERATING FACILITY EMERGENCY GENERATOR 17.110 1350 hp 41.9 LB/H N/A TX-0384 8/23/2000 10/26/2004 BRAZOS VALLEY ELECTRIC GENERATING FACILITY FIRE WATER PUMP 17.110 300 hp 9.3 LB/H N/A PA-0158 6/19/2000 12/2/2002 FORD ELECTRONICS AND REFRIGERATION, LLC DIESEL ENGINES 17.110 NO. 2 DIESEL 2 MW 20.8 LB/H Other Case-by- Case JOHNSON MATH

AND 3 DEGREE HOURLY LIMIT FANNUAL FOR A

VT-0013 6/8/2000 5/5/2003 MILL RIVER LUMBER, LTD. ELECTRIC GENERATION- CATERPILLAR 3412C 17.110 NO 2 FUEL OIL 1023 HP 1.7 LB/H Other Case-by- Case SCR W/OXIDAT

REGULATORY BMANUFACTURE

AK-0034 5/8/2000 3/26/2001 DILLINGHAM POWER PLANT IC ENGINES, DIESEL 17.110 DIESEL 21000000 KW-H/YR 21.9 LB/H BACT- PSD LEAN BURN/LOW 

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #3 17.110 DIESEL 350 KW

Other 

Case-byCase FOLLOW POWE

AS SPECIFIED I

Page 4 of 6
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.110, LARGE IC ENGINES >500 HP, 

FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 2, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONTR

THRUPUT EMISSIONS LIMIT

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #5 17.110 DIESEL 750 KW

Other 

Case-byCase FOLLOW POWE

AS SPECIFIED I

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #6 17.110 DIESEL 1000 KW

Other 

Case-byCase FOLLOW POWE

AS SPECIFIED I

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #8 17.110 DIESEL 835 KW

Other 

Case-byCase

FOLLOW THE PLIMITS SPECIFINOTES.

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #9 17.110 DIESEL 835 KW

Other 

Case-byCase FOLLOW POWE

AS SPECIFIED I

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR, #10 17.110 DIESEL 1135 KW

Other 

Case-byCase FOLLOW POWE

AS SPECIFIED I

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #11 17.110 DIESEL 1050 KW 24.9 LB/H BACT- PSD

FOLLOW POWE

AS SPECIFIED I

OPERATE LEAN ENGINE DESIGN 

AFTERCOOLER 

CONTROLS SET STRATEGY.

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #12 17.110 DIESEL 1050 KW 24.9 LB/H BACT- PSD

FOLLOW POWE

AS SPECIFIED I

OPERATE LEAN ENGINE DESIGN 

AFTERCOOLER 

CONTROLS SET STRATEGY.

AK-0043 5/8/2000 1/5/2005 DILLINGHAM POWER PLANT DIESEL ELECTRIC GENERATOR #13 17.110 DIESEL 1050 KW 24.9 LB/H BACT- PSD

FOLLOW POWE

AS SPECIFIED I

OPERATE WITH 

AFTERCOOLER 

CONTROLS SET STRATEGY.

CA-1083 3/30/2000 11/3/2005 CUCUMONGA COUNTY WATER DISTRICT ICE: EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 890 HP 6.9 G/B-HP/H BACT- PSD TURBOCHARCH

CA-1079 3/28/2000 5/2/2006 WALT DISNEY PICTURES AND TELEVISION ICE: EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 1109 HP 6.9 G/B-HP-H BACT- PSD TURBOCHARGE

OPERATIONS L

AK-0037 3/21/2000 1/5/2005 KENAI REFINERY UPPER TANK FARM CAT 3412DT, P708C 17.110 DIESEL 660 HP 3.1 LB/MMBTU N/A NONE INDICATEAK-0053 3/21/2000 1/5/2005 KENAI REFINERY EMERGENCY GENERATOR, CF-G-70003 17.110 FUEL OIL 2 MW 7 G/KW-H BACT- PSD

AFTER-COOLINPRESSURE FUEAND CYLINDER CLEAN BURN IN 

AK-0053 3/21/2000 1/5/2005 KENAI REFINERY EMERGENCY GENERATOR, CF-G-70004 17.110 FUEL OIL 2 MW 7 G/KW-H BACT- PSD

AFTER-COOLINPRESSURE FUEAND CYLINDER CLEAN BURN IN 

PR-0005 3/2/2000 8/31/2006 SAN JUAN REPOWERING PROJECT AUXILIARY DIESEL GENERATOR 17.110 DIESEL FUEL 5000 KW 168 LB/H (AS NO2) BACT- PSD GOOD COMBUS

CA-1080 2/22/2000 3/1/2006 HOMEGROCER.COM ICE: EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 1480 HP 6.9 G/B-HP-H BACT- PSD TURBOCHARGE

OPERATIONS L

CA-1082 2/1/2000 5/2/2006 CITY OF CORONA DEPT OF PUBLC WORKS ICE: EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 2155 HP 6.9 G/B-HP/H BACT- PSD TURBOCHARGE

OPERATIONS L

TX-0262 1/3/2000 10/7/2003 ARCHER GENERATING STATION EMERGENCY ELECTRICAL GENERATOR 17.110 DIESEL FUEL 2000 KW 46.8 LB/H BACT- PSD 

AK-0042 12/28/1999 9/29/2003 SNAKE RIVER POWER PLANT DIESEL ELECTRIC GENERATOR #9 17.110 DIESEL 2865 KW 106 LB/H BACT- PSD

OPERATE WITH DEGREES OF FRETARD AND WAFTERCOOLER COOLING WATEPOLLUTION CO

AK-0042 12/28/1999 9/29/2003 SNAKE RIVER POWER PLANT DIESEL ELECTRIC GENERATOR #11 17.110 DIESEL 1500 KW 62 LB/H BACT- PSD

OPERATE SOURLESS THAN 2 DINJECTION TIMIPOLLUTION CO

Page 5 of 6
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.110, LARGE IC ENGINES >500 HP, 

FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 2, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONTR

THRUPUT EMISSIONS LIMIT

AK-0042 12/28/1999 9/29/2003 SNAKE RIVER POWER PLANT DIESEL ELECTRIC GENERATOR #12A 17.110 DIESEL 3660 KW 188 LB/H BACT- PSD

OPERATE SOURLESS THAN 2.5 INJECTION TIMIPOLLUTION CO

AK-0042 12/28/1999 9/29/2003 SNAKE RIVER POWER PLANT DIESEL ELECTRIC GENERATOR #14 17.110 DIESEL 1875 KW 43 LB/H BACT- PSD GOOD AIR POLL

PRACTICES. 

AK-0042 12/28/1999 9/29/2003 SNAKE RIVER POWER PLANT DIESEL ELECTRIC GENERATOR #12B 17.110 DIESEL 4400 KW 203 LB/H BACT- PSD

OPERATE SOURTHAN 4 DEGRETIMING RETARDCONTROL PRAC

AK-0033 12/10/1999 1/30/2003 COMINCO RED DOG MINE IC ENGINE, DIESEL , WARTSILA 17.110 ARCTIC DIESEL 5 MW 121.3 LB/H BACT- PSD LOW NOX CONV

TX-0324 11/18/1999 1/25/2005 ODESSA-ECTOR GENERATING STATION EMERGENCY ELECTRICAL GENERATOR 17.110 DIESEL 2000 KW 46.8 LB/H BACT- PSD NONE INDICATE

CA-1078 11/9/1999 5/2/2006 INGRAM BOOK COMPANY ICE: EMERGENCY, COMPRESSION IGNITION 17.110 DIESEL 1448 BHP 6.9 G/B-HP-H BACT- PSD TURBOCHARGE

OPERATION LIM

TX-0321 10/12/1999 1/3/2005 CR WING COGENERATION PLANT STARTUP & EMERGENCY ELEC GENERATOR 17.110 DIESEL 2010 HP 54.5 LB/H Other Case-by- Case NONE INDICATE

MA-0029 9/29/1999 1/3/2003 SITHE MYSTIC DEVELOPMENT LLC IC ENGINE, EMERGENCY DIESEL GENERATOR 17.110 DIESEL 1500 KW 37.44 LB/H BACT- PSD SCR 

CA-0892 9/24/1999 10/3/2001 KIEWIT PACIFIC CO IC ENGINE, COMPRESSION IGNITION, PORTABLE 17.110 DIESEL 755 BHP 7 G/BHP-H BACT- PSD TURBOCHARGE

CA-0927 8/17/1999 12/3/2002 CHANNEL & BASIN RECLAMATION IC ENGINE, COMPRESSION IGNITION, DIESEL 17.110 DIESEL 810 BHP 5.4 G/B-HP-H BACT- PSD TURBOCHARGE

WITH TIMING REDEGREES FROM 

CA-1011 8/17/1999 10/27/2005 CHANNEL & BASIN RECLAMATION IC ENGINE, DIESEL 17.110 DIESEL 810 BHP 5.4 G/BHP-H BACT- PSD TURBOCHARGE

W/TIMING RETA

FL-0158 7/15/1999 3/28/2002 MIAMI-DADE WATER AND SEWER DEPARTMENT GENERATOR, DIESEL FUEL (4) 17.110 DIESEL 4000 BHP 4.12 LB/MMBTU BACT- PSD FUEL INJECTIO

AND TURBOCHA

IA-0072 7/8/1999 3/17/2005 GUARDIAN INDUSTRIES DIESEL GENERATOR 17.110 DIESEL FUEL 1750 KW 56.4 LB/H BACT- PSD 4 DEGREE RETA

TX-0291 5/7/1999 1/4/2005 TENASKA GATEWAY GENERATING STATION BLACK START GENERATOR NO.1, GEN 1, FUEL OIL 17.110 DIESEL 1.75 MW 58.7 LB/H BACT- PSD 

TX-0291 5/7/1999 1/4/2005 TENASKA GATEWAY GENERATING STATION BLACK START GENERATOR NO.2, GEN 2, FUEL OIL 17.110 DIESEL 1.75 MW 58.7 LB/H BACT- PSD MAX OPERATIO

TX-0291 5/7/1999 1/4/2005 TENASKA GATEWAY GENERATING STATION BLACK START GENERATOR NO.3, GEN 3, FUEL OIL 17.110 DIESEL 1.75 MW 58.7 LB/H BACT- PSD MAX OPERATIO

TX-0291 5/7/1999 1/4/2005 TENASKA GATEWAY GENERATING STATION BLACK START GENERATOR NO.4, GEN 4, FUEL OIL 17.110 DIESEL 1.75 MW 58.7 LB/H BACT- PSD MAX OPERATIO

TX-0291 5/7/1999 1/4/2005 TENASKA GATEWAY GENERATING STATION BLACK START GENERATOR NO.5, GEN 5, FUEL OIL 17.110 DIESEL 1.75 MW 58.7 LB/H BACT- PSD MAX OPERATIO

TX-0291 5/7/1999 1/4/2005 TENASKA GATEWAY GENERATING STATION BLACK START GENERATOR NO.6, GEN 6 17.110 FUEL OIL 1759 KW 58.7 LB/H BACT- PSD 

CA-0868 3/22/1999 10/11/2005 MANSON CONSTRUCTION COMPANY FOUR CATERPILLAR IC ENGINES 17.110 DIESEL FUEL 2600 HP 6.22 G/B-HP-H

Other 

Case-byCase SCR PROPOSED 

FL-0148 3/17/1999 6/5/2002 MIAMI-DADE WATER AND SEWER DEPT. GENERATORS, DIESEL (3) 17.110 DIESEL 2.5 MW 58 LB/H BACT- PSD INJECTION TIMI

COOLING OF CO

AK-0038 2/5/1999 1/5/2005 NORTHSTAR DEVELOPMENT PROJECT CAMP GENERATOR, UNIT 6,7 17.110 DIESEL 2362 KW 11 G/KW-H Other Case-by- Case VARIABLE FUEL 

RETARD AS INCMANUFACTURE

Control Category Key:GCP Good Combustion Practices

HIP High Injection PressureIAC Intake Air Cooling

ITR Ignition Timing Retard

LND Low NOx DesignNone No controls specified

SCR Selective Catalytic ReductionTier 1 or 2 Engine Emission Standards per 40 CFR 89 or 94

WI Water Injection

Page 6 of 6
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.210, SMALL IC ENGINES <= 500 HP, FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 6, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONT

SC-0113 2/8/2012 5/9/2012 PYRAMAX CERAMICS, LLC EMERGENCY ENGINE 1-8 17.210 DIESEL 29 HP 7.5 GR/KW-H BACT- PSD PURCHASE 

SC-0113 2/8/2012 5/9/2012 PYRAMAX CERAMICS, LLC FIRE PUMP 17.210 DIESEL 500 HP 4 GR/KW-H BACT- PSD PURCHASE 

BASED ON 

LA-0251 4/26/2011 12/12/2011 FLOPAM INC. FACILITY SMALL GENERATOR ENGINE 17.210 DIESEL 193 HP 1.28 LB/H BACT- PSD 

LA-0251 4/26/2011 12/12/2011 FLOPAM INC. FACILITY FIRE PUMP ENGINES - 2 UNITS 17.210 DIESEL 444 HP 5.82 LB/H BACT- PSD 

FL-0324 12/23/2010 12/8/2011 PALM BEACH RENEWABLE ENERGY PARK 250 KW EMERGENCY GENERATOR 17.210 ULTRA LOW SULFUR DISTILLATE 4 G/KW-H BACT- PSD USE OF INH

LOW SULFUFUEL OIL AN

ID-0018 6/25/2010 10/5/2010 LANGLEY GULCH POWER PLANT FIRE PUMP ENGINE 17.210 DIESEL 235 KW 4 G/KW-H BACT- PSD TIER 3 ENG

COMBUSTIO

*LA-0204 2/27/2009 8/6/2009 PLAQUEMINE PVC PLANT SMALL EMERGENCY ENGINES 17.210 DIESEL 4.41 LB/MMBTU BACT- PSD GOOD COM

AND GASEO

OK-0129 1/23/2009 2/18/2010 CHOUTEAU POWER PLANT EMERGENCY FIRE PUMP (267-HP DIESEL) 17.210 LOW SULFUR DIESEL 267 HP 4.59 LB/H BACT- PSD 

OH-0317 11/20/2008 2/20/2009 OHIO RIVER CLEAN FUELS, LLC FIRE PUMP ENGINES (2) 17.210 DIESEL FUEL OIL 300 HP 4.89 LB/H BACT- PSD

GOOD COMGOOD ENGTIMING RETAND LOW-TAFTERCOO

MD-0040 11/12/2008 2/20/2009 CPV ST CHARLES INTERNAL COMBUSTION ENGINE - EMERGENCY FIRE WATER PUMP 17.210 DIESEL 300 HP 3 G/HP-H BACT- PSD 

MD-0040 11/12/2008 2/20/2009 CPV ST CHARLES INTERNAL COMBUSTION ENGINE - EMERGENCY GENERATOR 17.210 DIESEL 4.8 G/HP-H BACT- PSD 

LA-0224 3/20/2008 6/26/2008 ARSENAL HILL POWER PLANT DFP DIESEL FIRE PUMP 17.210 DIESEL 310 HORSEPO WER 9.61 LB/H BACT- PSD USE OF LOW

LIMITING OPPROPER EN

*NV-0047 2/26/2008 10/21/2008 NELLIS AIR FORCE BASE SMALL INTERNAL COMBUSTION ENGINES (<= 500 HP) 17.210 DIESEL OIL 3.88 G/BHP-HR BACT- PSD TURBOCHA

AFTERCOO

CA-1144 4/25/2007 3/17/2008 BLYTHE ENERGY PROJECT II FIRE PUMP 17.210 DIESEL 303 HP 7.5 LB/H BACT- PSD 

AZ-0051 4/12/2006 8/6/2009 DRAKE EMERGENCY GENERATOR 17.210 FUEL OIL #2 210 KW 4 G/KW H BACT- PSD 

NC-0101 9/29/2005 8/30/2006 FORSYTH ENERGY PLANT IC ENGINE, EMERGENCY GENERATOR 17.210 DIESEL FUEL 11.4 MMBTU/H 36.5 LB/H BACT- PSD 

NC-0101 9/29/2005 8/30/2006 FORSYTH ENERGY PLANT IC ENGINE, EMERGENCY FIREWATER PUMP 17.210 DIESEL FUEL 11.4 MMBTU/H 36.5 LB/H BACT- PSD 

LA-0192 6/6/2005 4/8/2008 CRESCENT CITY POWER DIESEL FIRED WATER PUMP 17.210 8.9 LB/H BACT- PSD GOOD ENG

OPERATING 

MO-0067 12/29/2004 10/10/2006 SOUTH HARPER PEAKING FACILITY IC ENGINE, EMERGENCY DIESEL FIRE PUMP 17.210 DIESEL 0.47 mmbtu/h BACT- PSD IGNITION TI

OH-0252 12/28/2004 7/5/2005 DUKE ENERGY HANGING ROCK ENERGY FACILITY BACKUP GENERATORS (2) 17.210 DIESEL 500 KW 10.2 LB/H BACT- PSD 

OH-0252 12/28/2004 7/5/2005 DUKE ENERGY HANGING ROCK ENERGY FACILITY FIRE WATER PUMP (1) 17.210 DIESEL 265 HP 8.2 LB/H BACT- PSD 

*LA-0194 11/24/2004 9/3/2009 SABINE PASS LNG TERMINAL FIREWATER BOOSTER PUMP DIESEL ENGINES (2) 17.210 DIESEL 300 HP EACH 3.44 LB/H BACT- PSD GOOD ENG

OPERATING 

WI-0228 10/19/2004 8/31/2006 WPS - WESTON PLANT DIESEL BOOSTER PUMP (B27, S27) 17.210 DIESEL FUEL OIL 265 HP 8.21 LB/H BACT- PSD

GOOD COMWITH IGNITSULFUR (0.0OIL

WI-0228 10/19/2004 8/31/2006 WPS - WESTON PLANT MAIN FIRE PUMP (DIESEL ENGINE) 17.210 DIESEL FUEL OIL 460 HP 14.3 LB/H BACT- PSD

GOOD COMIGNITION TILOW SULFUFUEL OIL

WI-0227 10/13/2004 8/31/2006 PORT WASHINGTON GENERATING STATION DIESEL ENGINE GENERATOR (P05 / S05) 17.210 DIESEL FUEL OIL 7.6 MMBTU/H 27.4 LB/H BACT- PSD ENGINE DE

(0.05 WT.% 

OH-0275 8/24/2004 8/31/2006 PSI ENERGY-MADISON STATION EMERGENCY DIESEL FIRE PUMP 17.210 DIESEL FUEL 1.6 MMBTU/H 5.14 LB/H BACT- PSD 

OH-0281 6/10/2004 5/8/2007 RUMPKE SANITARY LANDFILL, INC PORTABLE ENGINE 0.58 MMBTU/H 17.210 FUEL OIL #2 0.58 MMBTU/H 2.55 LB/H BACT- PSD 

OH-0281 6/10/2004 5/8/2007 RUMPKE SANITARY LANDFILL, INC PORTABLE ENGINE 4.68 MMBTU/H 17.210 FUEL OIL #2 4.68 MMBTU/H 15 LB/H BACT- PSD 

THRUPUT EMISSIONS LIMIT 

Page 1 of 3
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.210, SMALL IC ENGINES <= 500 HP, FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 6, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONT

THRUPUT EMISSIONS LIMIT 

MI-0367 5/19/2004 10/25/2004 GM POWERTRAIN DIVISION ENGINE TEST CELLS/DYNAMOMETERS 17.210 DIESEL 303.33 MMBTU/H 1.38 LB/MMBTU BACT- PSD 

WV-0023 3/2/2004 2/3/2009 MAIDSVILLE IC ENGINE, FIRE WATER PUMP 17.210 DIESEL 85 HP 10.5 LB/H BACT- PSD COMBUSTIO

OPERATION

MN-0054 12/4/2003 8/24/2006 MANKATO ENERGY CENTER INTERNAL COMBUSTION ENGINE, SMALL 17.210 DIESEL FUEL 290 HP 5.7 G/B-HP-H BACT- PSD GOOD COMAK-0059 9/29/2003 5/22/2009 USAF EARECKSON AIR STATION IC ENGINES, FIREWATER PUMP, DIESEL, (2) 17.210 DIESEL BACT- PSD GOOD COMCA-1073 8/14/2003 2/14/2006 LOS ANGELES COUNTY PROBATION/FAC PLANNING/ISD ICE: FIRE PUMP, COMPRESSION IGNITION 17.210 DIESEL 240 BHP 4.2 G/B-HP-H BACT- PSD 5.5 DEGREE

TIMING RETRAW WATE

OH-0254 8/14/2003 7/5/2005 DUKE ENERGY WASHINGTON COUNTY LLC EMERGENCY DIESEL FIRE PUMP ENGINE 17.210 DIESEL 400 HP 12.8 LB/H BACT- PSD LOW SULFU

CONTROL 

MT-0022 7/21/2003 6/29/2004 BULL MOUNTAIN, NO. 1, LLC - ROUNDUP POWER PROJECT IC ENGINE, EMERGENCY GENERATOR 17.210 NO. 2 FUEL OIL 15.3 MMBTU/H 97.7 % REDUCTION BACT- PSD LIMITED HO

200 H/YR 

*IA-0067 6/17/2003 2/26/2009 MIDAMERICAN ENERGY COMPANY DIESEL FIRE PUMP 17.210 DIESEL FUEL 27.8 GAL/H 4.41 LB/MMBTU BACT- PSD GOOD COM

OK-0090 3/21/2003 10/10/2003 DUKE ENERGY STEPHENS, LLC STEPHENS ENERGY IC ENGINE, FIRE WATER PUMP 17.210 DIESEL 265 BHP 4.41 LB/MMBTU BACT- PSD ENGINE DE

(<100 H/YR) 

CA-0998 1/7/2003 9/4/2003 WESTERN DEVCON IC ENGINE 17.210 DIESEL FUEL 415 HP 6.9 G/B-HP-H LAER EPA CERTIFWA-0291 1/3/2003 8/31/2006 WALLULA POWER PLANT IC GENERATOR, EMERGENCY DIESEL 17.210 DIESEL 568 PPMDV @ 15% O2 Other Case-by- Case TX-0352 12/31/2002 5/24/2005 BRAZOS VALLEY ELECTRIC GENERATING FACILITY (2) FIRE WATER PUMPS, FWPUMP-1 & - 2 17.210 DIESEL 300 HP 9.3 LB/H BACT- PSD NONE INDIC

TX-0407 12/6/2002 10/26/2004 STERNE ELECTRIC GENERATING FACILITY FIRE WATER PUMP 17.210 DIESEL 300 HP 9.3 LB/H BACT- PSD 

CO-0052 8/11/2002 9/29/2003 ROCKY MOUNTAIN ENERGY CENTER, LLC. DISTILLATE FUEL OIL FIRED ENGINES (2) 17.210 DISTILLATE FUEL OIL 4.6 T/YR Other Case-by- Case 

CA-0991 8/9/2002 9/4/2003 CENIC DBA UC DAVIS COMMUNICATIONS RESOURCES IC ENGINES 17.210 DIESEL FUEL 277 HP 6.9 G/B-HP-H LAER OK-0070 6/13/2002 5/12/2004 GENOVA OK I POWER PROJECT DIESEL ENGINE, FIRE WATER PUMP 17.210 DIESEL FUEL 200 BHP 4.41 LB/MMBTU BACT- PSD ENGINE DE

HOURS 

CA-1075 5/14/2002 5/2/2006 ULTRAMAR INC. ICE: FIRE PUMP, COMPRESSION IGNITION 17.210 DIESEL 300 HP 5.89 G/B-HP-H BACT- PSD AIR/FUEL C

OPERATION

OK-0072 5/6/2002 7/7/2003 REDBUD POWER PLT DIESEL ENGINE, FIRE WATER PUMP 17.210 DIESEL 300 HP 0.03 LB/B-HP-H BACT- PSD 

CA-0989 5/1/2002 9/4/2003 FOLSOM SURGICAL CENTER IC ENGINE 17.210 DIESEL FUEL 68 HP 6.9 G/B-HP-H LAER IA-0058 4/10/2002 6/21/2004 GREATER DES MOINES ENERGY CENTER FIRE PUMP 17.210 DIESEL 235 BHP 2.55 LB/H BACT- PSD RETARDED 

DEGREES 

NJ-0043 3/28/2002 8/31/2006 LIBERTY GENERATING STATION EMERGENCY GENERATOR 17.210 DISTILLATE OIL 14.1 MMBTU/H 26.2 LB/H

Other Case-byCase NONE 

NJ-0043 3/28/2002 8/31/2006 LIBERTY GENERATING STATION DIESEL FIRE PUMP 17.210 DISTILLATE OIL 3.5 MMBTU/H 15.5 LB/H

Other Case-byCase NONE 

OK-0056 2/12/2002 5/6/2004 HORSESHOE ENERGY PROJECT DIESEL ENGINE, FIRE WATER PUMP 17.210 DIESEL FUEL 250 HP 4.41 LB/MMBTU BACT- PSD ENGINE DE

MD-0033 9/27/2001 3/1/2005 KELSON RIDGE EMERGENCY DIESEL GENERATOR 17.210 #2 FUEL OIL 700 KW LAER GOOD COM

OPERATION

MD-0033 9/27/2001 3/1/2005 KELSON RIDGE EMERGENCY DIESEL FIRE WATER PUMP 17.210 #2 FUEL OIL 200 HP LAER GOOD COM

OPERATION

LA-0122 8/14/2001 3/17/2005 MANSFIELD MILL CLARIFIER DIESEL ENGINE 17.210 DIESEL FUEL 310 HP 9.6 LB/H BACT- PSD PREVENTAT

LA-0122 8/14/2001 3/17/2005 MANSFIELD MILL WASTE CLARIFIER DIESEL ENGINE 17.210 DIESEL 413 HP 12.7 LB/H BACT- PSD PREVENTAT

LA-0122 8/14/2001 3/17/2005 MANSFIELD MILL EFFLUENT LIFT PIT DIESEL ENGINE 17.210 DIESEL FUEL 152 HP 4.7 LB/H BACT- PSD PREVENTAT

CA-1015 7/11/2001 10/28/2005

POWER SYSTEM ASSOCIATES/JOHNSON POWER SYSTEMS

IC ENGINE, EMERGENCY, COMPRESSION IGNITION 17.210 DIESEL 471 BHP 4.8 G/BHP-H BACT- PSD TURBOCHA

AFTERCOO

NJ-0044 6/26/2001 6/23/2004 MANTUA CREEK GENERATING FACILITY DIESEL FIRE PUMP 17.210 DIESEL (NO. 2 OIL) 1.5 MMBTU/H 3.35 LB/H N/A NONE 

NJ-0044 6/26/2001 6/23/2004 MANTUA CREEK GENERATING FACILITY EMERGENCY GENERATOR 17.210 DISTILLATE OIL 11.93 MMBTU/H 31 LB/H N/A NONE 

Page 2 of 3
EPA RACT/BACT/LAER CLEARINGHOUSE - NOx DETERMINATIONS

PROCESS CODE 17.210, SMALL IC ENGINES <= 500 HP, FUEL OIL (ASTM #1, 2, includes kerosene, aviation, diesel fuel), PERMITTED SINCE JANUARY 1, 1999

(searched October 6, 2009)

RBLC

ID 

PERMIT

ISSUED 

LAST

UPDATE FACILITY PERMITTED ITEM PROCESS TYPE FUEL LIMIT BASIS CONT

THRUPUT EMISSIONS LIMIT 

OK-0074 5/1/2001 5/6/2004 KIAMICHI ENERGY FACILITY DIESEL ENGINE, FIRE WATER PUMP 17.210 DIESEL 270 HP 29.8 LB/MMBTU BACT- PSD GOOD COM

AND DESIG

OK-0074 5/1/2001 5/6/2004 KIAMICHI ENERGY FACILITY DIESEL ENGINE, EMERGENCY GENERATOR 17.210 DIESEL 0.85 MMBUT/H 42 LB/MMBTU BACT- PSD GOOD COM

AND DESIG

OH-0255 3/29/2001 5/12/2008 AEP WATERFORD ENERGY LLC FIRE WATER PUMP 17.210 DIESEL 290 KW 0.24 T/YR BACT- PSD 

MD-0034 11/30/2000 3/1/2005 ROCK SPRINGS EMERGENCY DIESEL FIREWATER PUMP 17.210 #2 FUEL OIL 200 HP 10.5 G/B-HP-H LAER APPLICATIO

COMBUSTIOBURN TECH

TX-0326 7/20/2000 8/10/2006 AES WOLF HOLLOW LP EMERGENCY GENERATOR, E-GEN 17.210 310 KW 17.1 LB/H

Other Case-byCase NONE INDIC

TX-0326 7/20/2000 8/10/2006 AES WOLF HOLLOW LP EMERGENCY FIREWATER PUMP, E- PUMP 17.210 250 HP 2.4 LB/H Other Case-by- Case NONE INDICAK-0037 3/21/2000 1/5/2005 KENAI REFINERY ELECTRIC GENERATOR CAT 3412, EG704 17.210 DIESEL 4.8 MMBTU/H 3.1 LB/MMBTU N/A NONE INDIC

AK-0037 3/21/2000 1/5/2005 KENAI REFINERY NORTH CUMMINS, P708A 17.210 DIESEL 290 HP 4.41 LB/MMBTU N/A NONE INDICAK-0037 3/21/2000 1/5/2005 KENAI REFINERY SOUTH CUMMINS, P708B 17.210 DIESEL 290 HP 4.41 LB/MMBTU N/A NONE INDICTX-0273 3/21/2000 1/4/2005 BASTROP CLEAN ENERGY CENTER FIREWATER PUMP ENGINE 17.210 DIESEL FUEL 300 BHP 9.3 LB/H BACT- PSD 

TX-0262 1/3/2000 10/7/2003 ARCHER GENERATING STATION EMERGENCY FIREWATER PUMP 17.210 DIESEL 260 HP 8.1 LB/H BACT- PSD 

*AK-0033 12/10/1999 1/30/2003 COMINCO RED DOG MINE IC ENGINE , 200 HP, DIESEL ,CATERPILLAR 17.210 ARCTIC DIESEL 9 GAL/H 0.03 LB/HP-H BACT- PSD PERMIT LIM

*AK-0033 12/10/1999 1/30/2003 COMINCO RED DOG MINE IC ENGINE, DIESEL , CUMMINS/ONAN 17.210 ARCTIC DIESEL 188 KW 0.03 LB/HP-H BACT- PSD PERMIT LIM

*AK-0033 12/10/1999 1/30/2003 COMINCO RED DOG MINE IC ENGINE, 50 KW, DIESEL, DETROIT 17.210 ARCTIC DIESEL 9 GAL/H 0.03 LB/HP-H BACT- PSD PERMIT LIM

*AK-0033 12/10/1999 1/30/2003 COMINCO RED DOG MINE GENERATOR, DIESEL, 3208 TA CATERPILLAR 17.210 ARCTIC DIESEL 150 KW 0.03 LB/HP-H BACT- PSD EMISSION L*AK-0033 12/10/1999 1/30/2003 COMINCO RED DOG MINE IC ENGINE, DIESEL, 3406 CATERPILLAR, 2 UNITS 17.210 ARCTIC DIESEL 250 KW 0.03 LB/HP-H BACT- PSD PERMIT LIMTX-0324 11/18/1999 1/25/2005 ODESSA-ECTOR GENERATING STATION EMERGENCY FIREWATER PUMP, EG-2 17.210 DIESEL FUEL 260 HP 8.1 LB/H BACT- PSD NONE INDIC

CA-0906 11/16/1999 10/11/2005 RUNNING SPRINGS WATER DISTRICT IC ENGINE, COMPRESSION IGNITION, DIESEL 17.210 DIESEL 86 BHP 6.9 G/BHP-H BACT- PSD TURBOCHA

TIMING RET

CA-0926 11/10/1999 12/3/2002 KERN ASPHALT PAVING SEALING IC ENGINE, COMPRESSION IGNITION, DIESEL 17.210 DIESEL 460 BHP 6.9 G/B-HP-H BACT- PSD NO CONTROCA-0904 10/14/1999 10/11/2005 SANTA CLARITA VALLEY FOOD SERVICES IC ENGINE, COMPRESSION IGNITION, DIESEL 17.210 DIESEL 480 BHP 6.9 G/BHP-H BACT- PSD TURBOCHA

AFTERCOO

CA-0907 10/7/1999 10/11/2005 US GOVERNMENT NAVAL AIR STATION NORTH ISLAND IC ENGINE, COMPRESSION IGNITION, DIESEL 17.210 DIESEL 100 BHP 6.9 G/BHP-H BACT- PSD TURBOCHA

TIMING RET

CA-1077 10/7/1999 5/2/2006 US GOVERNMENT NAVAL AIR STATION, NORTH ISLAND ICE: EMERGENCY, COMPRESSION IGNITION 17.210 DIESEL 100 BHP 6.9 G/B-HP-H BACT- PSD INTERNAL C

TURBOCHALIMITED TO 

CA-0895 9/24/1999 10/11/2005 COACHELLA VALLEY WATER DISTRICT IC ENGINE, COMPRESSION IGNITION, DIESEL 17.210 DIESEL 325 BHP 6.9 G/BHP-H BACT- PSD 

CA-0896 8/18/1999 10/11/2005 CUMMINS CAL PACIFIC, INC. IC ENGINE, COMPRESSION IGNITION, DIESEL 17.210 DIESEL 68 BHP 6.9 G/BHP-H BACT- PSD NO CONTRO

NC-0078 6/30/1999 3/22/2004 ROCKINGHAM POWER, LLC POWER GENERATING IC ENGINE, EMERGENCY GENERATOR 17.210 NO. 2 FUEL OIL 250 KW 10.4 LB/H BACT- PSD LIMITED TO 

NC-0078 6/30/1999 3/22/2004 ROCKINGHAM POWER, LLC POWER GENERATING IC ENGINE, FIRE WATER PUMP 17.210 NO. 2 FUEL OIL 310 HP 9.6 LB/H BACT- PSD LIMITED TO 

Control Category Key:IAC Intake Air Cooling

GCP Good Combustion PracticesITR Ignition Timing RetardNone No controls specifiedTier 1 or 2 Engine Emission Standards per 40 CFR 89 or 94

Page 3 of 3