Name: Matthew Hockins

Title: Interim Environmental Contact

Company: Piney Creek Power Plant

Sign Date: 9/21/2010

Name: Eric S. White

Title: Project Manager

Company: Air/Compliance Consultants, Inc.

Sign Date: 9/21/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Piney Creek LP Emissions Testing Program

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 01, 2011 Page 1 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Facility Information:

Piney Creek LP

428 Power Lane

Clarion PA 16214

Contact: Matthew Hockins

Phone: 814-226-8001

Fax: 814-226-7909

Email: matt-pclp@csonline.net

Testing Company:

Air/Compliance Consultants, Inc.

1050 William Pitt Way

Pitsburgh PA 15238

Contact:Eric White

Phone: 412-826-3636

Fax: 412-826-3640

Email: ewhite@air-comp.com

Air Permit Number:

Title V 16-00127

Permitted Source ID/Name:

54144 Piney Creek Project

Permitted Maximum Process Rate:

450.00 MMBtu/hr

Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

The PCPP is an independent electrical power generating facility which uses energy from fuel oil, waste coal, wood 

waste, and non-hazardous organic tars/oils from manufactured gas and coke plants for transmission of electricity to 

the Reliant Energy, Piney Hydroelectric Power Plant substation interconnection. The facility produces a base load of 

32 MW net of electricity. Water is drawn from the Piney Reservoir on the Clarion River for boiler and cooling tower 

makeup, service water, and potable water. Waste coal fuel and limestone (for SO2 control) are delivered by truck to 

the site and ash products are trucked away for disposal. 

The facility includes one circulating fluidizing bed (CFB) boiler producing 290,000 pounds per hour (lb/hr) of steam 

at 1,310 pounds per square inch gauge (psig) pressure at 955°F. The boiler is manufactured by Tampella Power 

Corporation of Williamsport, Pennsylvania. The turbine-generator set is an Asea Brown Boveri VAX type unit 

exhausting steam at 2.5" mercury (Hg) to a water-cooled steam surface condenser. Flue gas from the boiler enters an 

8-module pulse jet-type fabric filter baghouse manufactured by Amerex, Inc. of Woodstock, Georgia. The design 

flow rate is 156,000 actual cubic feet per minute (ACFM) at 300°F with an inlet loading range of 8 to 30 

grains/ACFM of flyash. An induced draft fan draws flue gas from the baghouse and discharges it into the base of a 

275' tall concrete chimney.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110002348905 FRS #: 54144

SCC / Description 10100218 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Atmospheric Fluidized Bed Combustion: Circulating Bed (Bitum. Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

FBC 124 0 0 0 1956 1320 4 3

Tuesday, February 01, 2011 Page 2 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Test Parameter Information:

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

FBC Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

FBC Method 25A 3 120 0

FBC Hydrogen Chloride Method 26 3 240 0

FBC Hydrogen Fluoride Method 26 3 240 0

FBC Filterable PM2.5 OTM - 27/28 3 240 0

Organic Condensible 

Particulate

FBC OTM - 27/28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

FBC OTM - 27/28 3 240 0

FBC Chromium Method 29 3 240 0

FBC Antimony Method 29 3 240 0

FBC Arsenic Method 29 3 240 0

FBC Cadmium Method 29 3 240 0

FBC Cobalt Method 29 3 240 0

FBC Lead Method 29 3 240 0

FBC Manganese Method 29 3 240 0

FBC Selenium Method 29 3 240 0

FBC Nickel Method 29 3 240 0

FBC Filterable Particulate Method 29 3 240 0

FBC Phosphorus (yellow or white) Method 29 3 240 0

FBC Beryllium Method 29 3 240 0

FBC Sulfur Dioxide Method 6C 3 120 0

FBC Nitrogen oxides (NOx) Method 7E 3 120 0

Tuesday, February 01, 2011 Page 3 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Sampling / Stack Data Results Summary

Location FBC - Method 10

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/3/2010

Run Start Time 6:30:00 AM 8:42:00 

AM

10:52:00 AM

Run Finish Time 8:30:00 AM 10:42:00 

AM

12:52:00 PM

Carbon Dioxide, % 15.57 15.22 15.51 15.433

Oxygen, % 4.53 4.53 4.61 4.557

Dry Volumetric Flow Rate, dry scfm 100818 100904 106359 102,693.667

F-Factor, dscfm/MMBtu @ %O2 9740 9906 9829 9,825.000

Moisture, % 9.05 9.05 9.35 9.150

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location FBC - Method 25A

Average

Run Number 1 2 3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 6:45:00 AM 8:55:00 

AM

11:05:00 AM

Run Finish Time 8:45:00 AM 10:55:00 

AM

1:05:00 PM

Carbon Dioxide, % 14.81 14.73 14.58 14.707

Oxygen, % 4.62 4.7 4.72 4.680

Dry Volumetric Flow Rate, dry scfm 104021 103688 101597 103,102.000

F-Factor, dscfm/MMBtu @ %O2 9758 9698 9709 9,721.667

Moisture, % 8.29 9.38 6.87 8.180

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 4 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 26

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/4/2010

Run Start Time 8:55:00 AM 12:02:00 

PM

6:10:00 AM

Run Finish Time 11:55:00 AM 3:13:00 PM 9:10:00 AM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 124.637 124.947 122.805 124.130

Moisture Content of Stack Gas, % 9.17 9.29 9.66 9.373

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.56 15.61 15.24 15.470

Oxygen, % 4.6 4.56 4.71 4.623

Average Stack Gas Temperature, °F 347.58 348.89 340.42 345.630

Dry Volumetric Flow Rate, dry scfm 91,685.5 91,501.1 91,750.1 91,645.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 162,425.9 162,576.8 161,973.0 162,325.233

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2 9846 9639 9912 9,799.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location FBC - Method 29

Average

Run Number 1 2 3

Test Date 6/1/2010 6/2/2010 6/3/2010

Run Start Time 10:30:00 AM 7:15:00 

AM

6:30:00 AM

Run Finish Time 2:38:00 PM 3:47:00 PM 10:40:00 AM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 144.827 144.844 142.036 143.902

Moisture Content of Stack Gas, % 8.97 8.37 9.05 8.797

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.38 15.64 15.39 15.470

Oxygen, % 4.61 4.48 4.47 4.520

Average Stack Gas Temperature, °F 346.50 341.29 342.56 343.450

Dry Volumetric Flow Rate, dry scfm 94,879.8 93,729.3 91,779.9 93,463.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 166,904.1 162,174.3 161,369.2 163,482.533

Percent Isokinetic of Sampling Rate, % 98.6 99.8 99.9 99.433

F-Factor, dscfm/MMBtu @ %O2 9871 9864 9617 9,784.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 5 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 6C

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/3/2010

Run Start Time 6:30:00 AM 8:42:00 

AM

10:52:00 AM

Run Finish Time 8:30:00 AM 10:42:00 

AM

12:52:00 PM

Carbon Dioxide, % 15.57 15.22 15.51 15.433

Oxygen, % 4.53 4.53 4.61 4.557

Dry Volumetric Flow Rate, dry scfm 100818 100904 106359 102,693.667

F-Factor, dscfm/MMBtu @ %O2 9740 9906 9829 9,825.000

Moisture, % 9.05 9.05 9.35 9.150

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location FBC - Method 7E

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/3/2010

Run Start Time 6:30:00 AM 8:42:00 

AM

10:52:00 AM

Run Finish Time 8:30:00 AM 10:42:00 

AM

12:52:00 PM

Carbon Dioxide, % 15.57 15.22 15.51 15.433

Oxygen, % 4.53 4.53 4.61 4.557

Dry Volumetric Flow Rate, dry scfm 100818 100904 106359 102,693.667

F-Factor, dscfm/MMBtu @ %O2 9740 9906 9906 9,850.667

Moisture, % 9.05 9.05 9.35 9.150

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 6 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - OTM - 27/28

Average

Run Number 1 2 3

Test Date 6/1/2010 6/2/2010 6/3/2010

Run Start Time 9:30:00 AM 6:00:00 

AM

6:30:00 AM

Run Finish Time 3:49:00 PM 3:54:00 PM 12:46:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 134.213 133.223 137.065 134.834

Moisture Content of Stack Gas, % 8.26 8.16 9.01 8.477

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.4 15.61 9.27 13.427

Oxygen, % 4.59 4.52 4.45 4.520

Average Stack Gas Temperature, °F 350.75 327.83 347.83 342.137

Dry Volumetric Flow Rate, dry scfm 97,957.5 99,729.2 100,156.2 99,280.967

Actual Wet Volumetric Flue Gas Flow Rate, acfm 171,885.6 169,269.1 170,577.3 170,577.333

Percent Isokinetic of Sampling Rate, % 641.2 625.2 640.5 635.633

F-Factor, dscfm/MMBtu @ %O2 9689 9658 9732 9,693.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 7 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Emissions Summary

Location: FBC - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 6.93E-02 6.51E-02 6.27E-02 0.066

ppm 7.66E+01 7.09E+01 6.84E+01 71.967

ppm@7%O2 6.50E+01 6.02E+01 5.84E+01 61.200

Location: FBC - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 1.32E-03 1.18E-03 9.42E-04 0.001

Location: FBC - Method 26

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.61 180 180 120.203

lb/mmBtuO2 1.36E-04 3.92E-02 4.13E-02 0.027

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 160 0.55 0.63 53.727

lb/mmBtuO2 3.57E-02 1.20E-04 1.45E-04 0.012

Location: FBC - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0028 0.0028 0.0028 0.003

lb/mmBtuO2 5.40E-07 5.35E-07 5.32E-07 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00564 0.00351 0.00382 0.004

lb/mmBtuO2 1.09E-06 6.71E-07 7.25E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00075 0.0007 0.0007 0.001

lb/mmBtuO2 1.45E-07 1.34E-07 1.33E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Tuesday, February 01, 2011 Page 8 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Mass_mg 0.00075 0.001 0.00079 0.001

lb/mmBtuO2 1.45E-07 1.91E-07 1.50E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.029 0.01097 0.00857 0.016

lb/mmBtuO2 5.59E-06 2.10E-06 1.63E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00462 0.00086 0.00093 0.002

lb/mmBtuO2 8.91E-07 1.64E-07 1.77E-07 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 16.19 17.52 27.78 20.497

lb/mmBtuO2 3.12E-03 3.35E-03 5.27E-03 0.004

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.01584 0.00252 0.00395 0.007

lb/mmBtuO2 3.05E-06 4.82E-07 7.50E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0265 0.0186 0.0234 0.023

lb/mmBtuO2 5.11E-06 3.55E-06 4.44E-06 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0187 0.0159 0.0067 0.014

lb/mmBtuO2 3.61E-06 3.04E-06 1.27E-06 0.000

Compound: Phosphorus (yellow or white)

Average

RunNumber 1 2 3

Mass_mg 0.067 0.051 0.052 0.057

lb/mmBtuO2 1.29E-05 9.75E-06 9.87E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.007 0.0087 0.007 0.008

lb/mmBtuO2 1.35E-06 1.66E-06 1.33E-06 0.000

Location: FBC - Method 6C

Tuesday, February 01, 2011 Page 9 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Process Run Data

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 5.68E-01 5.28E-01 6.39E-01 0.578

ppm 2.75E+02 2.51E+02 3.05E+02 277.000

ppm@7%O2 2.34E+02 2.13E+02 2.60E+02 235.667

Location: FBC - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 1.05E-01 1.04E-01 1.03E-01 0.104

ppm 7.06E+01 6.91E+01 6.77E+01 69.133

ppm@7%O2 5.99E+01 5.87E+01 5.78E+01 58.800

Location: FBC - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 26.66 42.15 32.05 33.620

lb/mmBtuO2 5.44E-03 8.60E-03 6.37E-03 0.007

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 19.47 32.87 24.16 25.500

lb/mmBtuO2 3.97E-03 6.70E-03 4.80E-03 0.005

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 4.85 4.85 7.3 5.667

lb/mmBtuO2 9.89E-04 9.89E-04 1.45E-03 0.001

Tuesday, February 01, 2011 Page 10 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 0 Tons/hr 0

Run Name Value UOM Comments

Target

Value

1 FLUID BED DRY SCRUBBER 0 0

Tuesday, February 01, 2011 Page 11 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Sampling / Stack Data Results Detail

Location FBC - Method 10

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/3/2010

Run Start Time 6:30:00 AM 8:42:00 AM 10:52:00 AM

Run Finish Time 8:30:00 AM 10:42:00 AM 12:52:00 PM

Carbon Dioxide, % 15.57 15.22 15.51 15.433

Oxygen, % 4.53 4.53 4.61 4.557

Fuel Factor 1.05 1.08 1.05

Dry Volumetric Flow Rate, dry scfm 100818 100904 106359 102,693.667

F-Factor, dscfm/MMBtu @ %O2 9740 9906 9829 9,825.000

Moisture, % 9.05 9.05 9.35 9.150

Analyzer Make TECO TECO TECO

Analyzer Model 48C 48C 48C

Analyzer Serial Number 48CHL64485-34448CHL64485-34448CHL64485-344

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0 1 0.3 0.433

Calibration Pre Zero Cylinder Bias 0 1 0.3 0.433

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC4117 Mid 

CO

CC4117 

Mid CO

CC4117 Mid 

CO

Calibration Pre High Cylinder Instrument Response 50.1 51 50.8 50.633

Calibration Pre High Cylinder Bias 0.2 1.1 0.9 0.733

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 1 0.3 0.7 0.667

Calibration Post Zero Cylinder Bias 1 0.3 0.7 0.667

Calibration Post Zero Cylinder Drift 1 0.7 0.4 0.700

Calibration Post High Cylinder ID CC4117 Mid 

CO

CC4117 

Mid CO

CC4117 Mid 

CO

Calibration Post High Cylinder Instrument Response 51 50.8 50.1 50.633

Calibration Post High Cylinder Bias 1.1 0.9 0.2 0.733

Calibration Post High Cylinder Drift 0.9 0.2 0.7 0.600

Cavg 77.19 71.86 68.88 72.643

Cavg Units ppmvd ppmvd ppmvd

Cgas 76.6134 70.8557 68.4484 71.973

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 01, 2011 Page 12 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 25A

Average

Run Number 1 2 3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 6:45:00 AM 8:55:00 AM 11:05:00 AM

Run Finish Time 8:45:00 AM 10:55:00 AM 1:05:00 PM

Carbon Dioxide, % 14.81 14.73 14.58 14.707

Oxygen, % 4.62 4.7 4.72 4.680

Fuel Factor 1.1 1.1 1.11

Dry Volumetric Flow Rate, dry scfm 104021 103688 101597 103,102.000

F-Factor, dscfm/MMBtu @ %O2 9758 9698 9709 9,721.667

Moisture, % 8.29 9.38 6.87 8.180

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 40 40 40 40.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0.04 0.05 0.06 0.050

Calibration Pre Zero Cylinder Bias 0 0.1 0.2 0.100

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID XC009797B 

Mid THC

XC009797B 

Mid THC

XC009797B 

Mid THC

Calibration Pre High Cylinder Instrument Response 5 4.95 4.91 4.953

Calibration Pre High Cylinder Bias 0 -0.5 -0.9 -0.467

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0.05 0.06 0.06 0.057

Calibration Post Zero Cylinder Bias 0.1 0.2 0.2 0.167

Calibration Post Zero Cylinder Drift 0.1 0.1 0 0.067

Calibration Post High Cylinder ID XC009797B 

Mid THC

XC009797B 

Mid THC

XC009797B 

Mid THC

Calibration Post High Cylinder Instrument Response 4.95 4.91 4.96 4.940

Calibration Post High Cylinder Bias -0.5 -0.9 -0.4 -0.600

Calibration Post High Cylinder Drift 0.5 0.4 0.5 0.467

Cavg 0.95 0.86 0.7 0.837

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.9178 0.8256 0.6564 0.800

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 01, 2011 Page 13 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 26

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/4/2010

Run Start Time 8:55:00 AM 12:02:00 PM 6:10:00 AM

Run Finish Time 11:55:00 AM 3:13:00 PM 9:10:00 AM

Net Traversing Points 36 36 36

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.998 0.998 0.998 0.998

Barometric Pressure, inches of Mercury 28.45 28.45 28.45 28.450

Average Orifice Meter Differential, inches H2O 1.70 1.70 1.70 1.700

Dry Gas Meter Volume Sampled, cubic feet 133.274 135.522 131.503 133.433

Average Dry Gas Meter Temperature, °F 78.13 85.85 78.90 80.960

Dry Gas Meter Volume Sampled, dscf 124.637 124.947 122.805 124.130

Total Moisture Liquid collected, g 267.5 271.7 278.9 272.700

Volume of Water Vapor, standard cubic feet 12.59 12.79 13.13 12.837

Moisture Content of Stack Gas, % 9.17 9.29 9.66 9.373

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9083 0.9071 0.9034 0.906

Carbon Dioxide, % 15.56 15.61 15.24 15.470

Oxygen, % 4.6 4.56 4.71 4.623

Carbon Monoxide & Nitrogen, % 79.84 79.83 80.05 79.907

Fuel Factor 1.05 1.05 1.06

Dry Molecular Weight, lb/lb-Mole 30.67 30.68 30.63 30.660

Wet Molecular weight, lb/lb-Mole 29.51 29.50 29.41 29.473

Flue Gas Static Pressure, inches of H2O -0.15 -0.15 -0.16 -0.153

Absolute Flue Gas Pressure, inches of Mercury 28.44 28.44 28.44 28.440

Average Stack Gas Temperature, °F 347.58 348.89 340.42 345.630

Average Velocity Head, inches of H2O 0.21 0.21 0.21 0.210

Average Stack Gas Velocity, feet/second 32.28 32.31 32.19 32.260

Stack Cross-Sectional Area, square feet 83.863 83.863 83.863 83.863

Dry Volumetric Flow Rate, dry scfm 91,685.5 91,501.1 91,750.1 91,645.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 162,425.9 162,576.8 161,973.0 162,325.233

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, % 27.9 27.6 28.7 28.067

F-Factor, dscfm/MMBtu @ %O2 9846 9639 9912 9,799.000

Round Duct Diameter, inches 124 124 124

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 14 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 29

Average

Run Number 1 2 3

Test Date 6/1/2010 6/2/2010 6/3/2010

Run Start Time 10:30:00 AM 7:15:00 AM 6:30:00 AM

Run Finish Time 2:38:00 PM 3:47:00 PM 10:40:00 AM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.315 0.315 0.315 0.315

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.998 0.998 0.998 0.998

Barometric Pressure, inches of Mercury 28.55 28.65 28.45 28.550

Average Orifice Meter Differential, inches H2O 1.24 1.17 1.13 1.180

Dry Gas Meter Volume Sampled, cubic feet 155.464 155.384 152.868 154.572

Average Dry Gas Meter Temperature, °F 81.47 82.92 80.84 81.743

Dry Gas Meter Volume Sampled, dscf 144.827 144.844 142.036 143.902

Total Moisture Liquid collected, g 303.1 281.1 300.1 294.767

Volume of Water Vapor, standard cubic feet 14.27 13.23 14.13 13.877

Moisture Content of Stack Gas, % 8.97 8.37 9.05 8.797

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9103 0.9163 0.9095 0.912

Carbon Dioxide, % 15.38 15.64 15.39 15.470

Oxygen, % 4.61 4.48 4.47 4.520

Carbon Monoxide & Nitrogen, % 80.01 79.88 80.14 80.010

Fuel Factor 1.06 1.05 1.07

Dry Molecular Weight, lb/lb-Mole 30.65 30.68 30.64 30.657

Wet Molecular weight, lb/lb-Mole 29.52 29.62 29.50 29.547

Flue Gas Static Pressure, inches of H2O -0.15 -0.15 -0.16 -0.153

Absolute Flue Gas Pressure, inches of Mercury 28.54 28.64 28.44 28.540

Average Stack Gas Temperature, °F 346.50 341.29 342.56 343.450

Average Velocity Head, inches of H2O 0.2229101363

2974

0.213223463

623296

0.208477012

459346

0.215

Average Stack Gas Velocity, feet/second 33.17 32.23 32.07 32.490

Stack Cross-Sectional Area, square feet 83.863 83.863 83.863 83.863

Dry Volumetric Flow Rate, dry scfm 94,879.8 93,729.3 91,779.9 93,463.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 166,904.1 162,174.3 161,369.2 163,482.533

Percent Isokinetic of Sampling Rate, % 98.6 99.8 99.9 99.433

Percent Excess Air, % 27.9 27.0 26.8 27.233

F-Factor, dscfm/MMBtu @ %O2 9871 9864 9617 9,784.000

Round Duct Diameter, inches 124 124 124

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 15 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 6C

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/3/2010

Run Start Time 6:30:00 AM 8:42:00 AM 10:52:00 AM

Run Finish Time 8:30:00 AM 10:42:00 AM 12:52:00 PM

Carbon Dioxide, % 15.57 15.22 15.51 15.433

Oxygen, % 4.53 4.53 4.61 4.557

Fuel Factor 1.05 1.08 1.05

Dry Volumetric Flow Rate, dry scfm 100818 100904 106359 102,693.667

F-Factor, dscfm/MMBtu @ %O2 9740 9906 9829 9,825.000

Moisture, % 9.05 9.05 9.35 9.150

Analyzer Make Western 

Research

Western 

Research

Western 

Research

Analyzer Model

Analyzer Serial Number 92721AT2795

0-1

92721AT279

50-1

92721AT279

50-1

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 10 10 10 10.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0.3 1.5 0.8 0.867

Calibration Pre Zero Cylinder Bias 0.06 0.3 0.16 0.173

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275965 

mid

CC275965 

mid

CC275965 

mid

Calibration Pre High Cylinder Instrument Response 251.9 250.2 250.2 250.767

Calibration Pre High Cylinder Bias 0.16 -0.18 -0.18 -0.067

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 1.5 0.8 0.2 0.833

Calibration Post Zero Cylinder Bias 0.3 0.16 0.04 0.167

Calibration Post Zero Cylinder Drift 0.24 0.14 0.12 0.167

Calibration Post High Cylinder ID CC275965 

mid

CC275965 

mid

CC275965 

mid

Calibration Post High Cylinder Instrument Response 250.2 250.2 247 249.133

Calibration Post High Cylinder Bias -0.18 -0.18 -0.83 -0.397

Calibration Post High Cylinder Drift 0.34 0 0.65 0.330

Cavg 275.89 251.46 302.8 276.717

Cavg Units ppmvd ppmvd ppmvd

Cgas 274.8251 251.2648 304.6151 276.902

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 01, 2011 Page 16 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - Method 7E

Average

Run Number 1 2 3

Test Date 6/3/2010 6/3/2010 6/3/2010

Run Start Time 6:30:00 AM 8:42:00 AM 10:52:00 AM

Run Finish Time 8:30:00 AM 10:42:00 AM 12:52:00 PM

Carbon Dioxide, % 15.57 15.22 15.51 15.433

Oxygen, % 4.53 4.53 4.61 4.557

Fuel Factor 1.05 1.08 1.05

Dry Volumetric Flow Rate, dry scfm 100818 100904 106359 102,693.667

F-Factor, dscfm/MMBtu @ %O2 9740 9906 9906 9,850.667

Moisture, % 9.05 9.05 9.35 9.150

Analyzer Make TECO TECO TECO

Analyzer Model 42CHL 42CHL 42CHL

Analyzer Serial Number 62298-334 62298-334 62298-334

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 20 20 20 20.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0 1 1 0.667

Calibration Pre Zero Cylinder Bias 0 0.5 0.5 0.333

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC176769 

Mid Nox

CC176769 

Mid Nox

CC176769 

Mid Nox

Calibration Pre High Cylinder Instrument Response 100 99 100 99.667

Calibration Pre High Cylinder Bias -0.5 -1 -0.5 -0.667

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 1 1 1 1.000

Calibration Post Zero Cylinder Bias 0.5 0.5 0.5 0.500

Calibration Post Zero Cylinder Drift 0.5 0 0 0.167

Calibration Post High Cylinder ID CC176769 

Mid Nox

CC176769 

Mid Nox

CC176769 

Mid Nox

Calibration Post High Cylinder Instrument Response 99 100 99.8 99.600

Calibration Post High Cylinder Bias -1 -0.5 -0.6 -0.700

Calibration Post High Cylinder Drift 0.5 0.5 0.1 0.367

Cavg 70.38 69.08 67.94 69.133

Cavg Units ppmvd ppmvd ppmvd

Cgas 70.5859 69.1168 67.6845 69.129

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 01, 2011 Page 17 of 18
Piney Creek LP Emissions Testing Program

9/21/2010

Location FBC - OTM - 27/28

Average

Run Number 1 2 3

Test Date 6/1/2010 6/2/2010 6/3/2010

Run Start Time 9:30:00 AM 6:00:00 AM 6:30:00 AM

Run Finish Time 3:49:00 PM 3:54:00 PM 12:46:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.234 0.234 0.234 0.234

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1 1 1 1.000

Barometric Pressure, inches of Mercury 28.55 28.65 29.6 28.933

Average Orifice Meter Differential, inches H2O 0.45 0.45 0.45 0.450

Dry Gas Meter Volume Sampled, cubic feet 140.613 138.584 138.610 139.269

Average Dry Gas Meter Temperature, °F 68.46 66.54 68.83 67.943

Dry Gas Meter Volume Sampled, dscf 134.213 133.223 137.065 134.834

Total Moisture Liquid collected, g 256.9 251.5 288.4 265.600

Volume of Water Vapor, standard cubic feet 12.09 11.84 13.57 12.500

Moisture Content of Stack Gas, % 8.26 8.16 9.01 8.477

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9174 0.9184 0.9099 0.915

Carbon Dioxide, % 15.4 15.61 9.27 13.427

Oxygen, % 4.59 4.52 4.45 4.520

Carbon Monoxide & Nitrogen, % 80.01 79.87 86.28 82.053

Fuel Factor 1.06 1.05 1.77

Dry Molecular Weight, lb/lb-Mole 30.65 30.68 29.66 30.330

Wet Molecular weight, lb/lb-Mole 29.61 29.65 28.61 29.290

Flue Gas Static Pressure, inches of H2O -0.16 -0.15 -0.8 -0.370

Absolute Flue Gas Pressure, inches of Mercury 28.54 28.64 29.54 28.907

Average Stack Gas Temperature, °F 350.75 327.83 347.83 342.137

Average Velocity Head, inches of H2O 0.2357902555

98165

0.236571758

3127

0.233202422

460978

0.235

Average Stack Gas Velocity, feet/second 34.16 33.64 33.90 33.900

Stack Cross-Sectional Area, square feet 83.863 83.863 83.863 83.863

Dry Volumetric Flow Rate, dry scfm 97,957.5 99,729.2 100,156.2 99,280.967

Actual Wet Volumetric Flue Gas Flow Rate, acfm 171,885.6 169,269.1 170,577.3 170,577.333

Percent Isokinetic of Sampling Rate, % 641.2 625.2 640.5 635.633

Percent Excess Air, % 27.8 27.3 24.3 26.467

F-Factor, dscfm/MMBtu @ %O2 9689 9658 9732 9,693.000

Round Duct Diameter, inches 124 124 124

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 18 of 18