Name: Lois A. Knowlson

Title: Senior Environmental Engineer

Company: PSEG Environmental

Sign Date: 9/3/2010

Name: Anthony Fortunato

Title: Senior Testing Supervisor

Company: Maplewood Testing Services

Sign Date: 9/3/2010

Permitted Facility Representative / Date Testing Company Representative / Date

PSEG Sewaren Unit 4

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 22, 2011 Page 1 of 45
PSEG Sewaren Unit 4

9/3/2010

Facility Information:

PSEG Sewaren Generating Station 2411

751 Cliff Road

Sewaren NJ 07077

Contact: Joseph D. Krejsa

Phone: 732-750-2001

Fax:

Email: joseph.krejsa@pseg.com

Testing Company:

PSEG Maplewood Testing Services

200 Boyden Avenue

Maplewood NJ 07040

Contact: Anthony Fortunato

Phone: 973-761-1005

Fax:

Email: anthony.fortunato2@pseg.com

Air Permit Number:

2411-BOP08001

Permitted Source ID/Name:

U4 Unit 4

Permitted Maximum Process Rate:

1700 MMBtu/hr

Max. Normal Operation Process Rate:

1700 MMBtu/hr

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Sewaren Unit 4 is a dual-fuel (natural gas and #6 fuel oil) single-furnance, wet bottom, balanced draft, two-drum 

natural circulation steam generator with vertically adjustable tangential corner burners manufactured by Combustion 

Engineering (July 1951) for electricity generation. No emissions control devices are installed on this unit.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000869150 FRS #: 110000801614

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 14.263 151.7 151.7 14.263 487 1579 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Regulation Description Compound Limit Unit

NJAC 7:27-4.2(a) Particulate 160 lb/hr

NJAC 7:27-16.8(b)1 Volatile Organic 

Compounds (total)

50 ppm corrected

NJAC 7:27-16.8(b)2 Carbon Monoxide 100 ppm corrected

Tuesday, February 22, 2011 Page 2 of 45
PSEG Sewaren Unit 4

9/3/2010

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 0 PSEG believes that the 

Method 25A THC test 

results for Run 1-1 

should be 4.65E-4 

lb/mmBtu and 1.89E1 lb/hr. PSEG unable 

to determine why the 

ERT is reporting 

2.32E-4 lb/mmBtu 

and 0.095 lb/hr.

Stack Exit

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Tuesday, February 22, 2011 Page 3 of 45
PSEG Sewaren Unit 4

9/3/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Cobalt Method 29 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit O2 Method 3A O2 3 120 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit Co2 Method 3A CO2 3 240 0

Stack Exit O2 Method 3A O2 3 480 0

Stack Exit Co2 Method 3A CO2 3 480 0

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Filterable Particulate Method 5 3 240 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Tuesday, February 22, 2011 Page 4 of 45
PSEG Sewaren Unit 4

9/3/2010

Tuesday, February 22, 2011 Page 5 of 45
PSEG Sewaren Unit 4

9/3/2010

Tuesday, February 22, 2011 Page 6 of 45
PSEG Sewaren Unit 4

9/3/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:06:00 AM 10:08:00 

AM

1:18:00 PM

Run Finish Time 9:22:00 AM 12:22:00 

PM

3:31:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 72.146 70.865 74.042 72.351

Moisture Content of Stack Gas, % 5.41 5.47 5.79 5.557

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Average Stack Gas Temperature, °F 214.33 219.04 222.92 218.763

Dry Volumetric Flow Rate, dry scfm 229,463.3 222,694.8 230,858.0 227,672.033

Actual Wet Volumetric Flue Gas Flow Rate, acfm 312,112.8 305,113.1 319,400.3 312,208.733

Percent Isokinetic of Sampling Rate, % 96.5 97.7 98.5 97.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 10

Average

Run Number 1-1 1-2 1-3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:15:00 AM 10:10:00 

AM

1:19:00 PM

Run Finish Time 9:19:00 AM 12:14:00 

PM

3:23:00 PM

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Dry Volumetric Flow Rate, dry scfm 229604.2 222554.8 230858 227,672.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.41 5.47 5.79 5.557

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 7 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 6/1/2010 6/2/2010 6/3/2010

Run Start Time 6:00:00 AM 7:40:00 

AM

2:27:00 AM

Run Finish Time 9:45:00 PM 11:16:00 

PM

6:12:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 287.092 305.056 297.596 296.581

Moisture Content of Stack Gas, % 5.36 5.22 4.99 5.190

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 4.225 4.249 4.276 4.250

Oxygen, % 15.277 15.294 15.195 15.255

Average Stack Gas Temperature, °F 213.63 217.63 303.25 244.837

Dry Volumetric Flow Rate, dry scfm 222,691.2 235,198.5 217,976.2 225,288.633

Actual Wet Volumetric Flue Gas Flow Rate, acfm 303,962.4 321,701.6 335,797.0 320,487.000

Percent Isokinetic of Sampling Rate, % 99.0 99.6 104.1 100.900

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 25A

Average

Run Number 1-1 1-2 1-3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:15:00 AM 10:10:00 

AM

1:19:00 PM

Run Finish Time 9:19:00 AM 12:14:00 

PM

3:23:00 PM

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Dry Volumetric Flow Rate, dry scfm 229604.2 222554.8 230858 227,672.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.41 5.47 5.79 5.557

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 8 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 6/1/2010 6/1/2010 6/3/2010

Run Start Time 9:12:00 AM 11:38:00 

AM

3:59:00 PM

Run Finish Time 10:34:00 AM 12:48:00 

PM

5:09:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 36.769 37.781 36.104 36.885

Moisture Content of Stack Gas, % 7.71 7.72 7.48 7.637

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 4.096 4.266 4.346 4.236

Oxygen, % 15.37 15.257 15.192 15.273

Average Stack Gas Temperature, °F 229.83 218.21 229.42 225.820

Dry Volumetric Flow Rate, dry scfm 222,153.7 236,198.5 219,561.1 225,971.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 315,756.5 331,769.7 313,742.9 320,423.033

Percent Isokinetic of Sampling Rate, % 101.6 98.2 100.3 100.033

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 9 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 29 

Average

Run Number 2 3 4

Test Date 6/2/2010 6/2/2010 6/3/2010

Run Start Time 9:25:00 AM 4:10:00 PM 9:00:00 AM

Run Finish Time 3:19:00 PM 10:02:00 

PM

2:49:00 PM

Net Run Time, minutes 336 336 336

Dry Gas Meter Volume Sampled, dscf 219.573 218.882 216.450 218.302

Moisture Content of Stack Gas, % 7.06 6.81 7.13 7.000

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 6.2 6.2 6.4 6.267

Oxygen, % 12.8 12.7 12.5 12.667

Average Stack Gas Temperature, °F 240.75 242.54 243.63 242.307

Dry Volumetric Flow Rate, dry scfm 312,401.1 311,651.5 310,152.5 311,401.700

Actual Wet Volumetric Flue Gas Flow Rate, acfm 448,656.2 448,272.7 449,711.0 448,879.967

Percent Isokinetic of Sampling Rate, % 99.7 99.6 99.0 99.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 6C

Average

Run Number 1-1 1-2 1-3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:15:00 AM 10:10:00 

AM

1:19:00 PM

Run Finish Time 9:14:00 AM 12:14:00 

PM

3:23:00 PM

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Dry Volumetric Flow Rate, dry scfm 224759.9 217795.8 226006.6 222,854.100

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.41 5.47 5.79 5.557

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 10 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 6C 3

Average

Run Number 3-1 3-2 3-3

Test Date 6/1/2010 6/1/2010 6/3/2010

Run Start Time 9:14:00 AM 11:40:00 

AM

4:01:00 PM

Run Finish Time 10:20:00 AM 12:40:00 

PM

5:11:00 PM

Carbon Dioxide, % 4.096 4.266 4.346 4.236

Oxygen, % 15.37 15.257 15.192 15.273

Dry Volumetric Flow Rate, dry scfm 222153.7 235993.7 219494 225,880.467

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 7.71 7.72 7.78 7.737

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 7E

Average

Run Number 3-1 3-2 3-3

Test Date 6/1/2010 6/1/2010 6/3/2010

Run Start Time 9:14:00 AM 11:40:00 

AM

4:01:00 PM

Run Finish Time 10:20:00 AM 12:40:00 

PM

5:11:00 PM

Carbon Dioxide, % 4.096 4.266 4.346 4.236

Oxygen, % 15.37 15.257 15.192 15.273

Dry Volumetric Flow Rate, dry scfm 219995.4 231026.6 218381 223,134.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 7.71 7.72 7.78 7.737

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 11 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - OTM - 27/28

Average

Run Number 2 3 4

Test Date 6/2/2010 6/2/2010 6/3/2010

Run Start Time 9:25:00 AM 4:10:00 PM 9:00:00 AM

Run Finish Time 3:13:00 PM 10:04:00 

PM

2:40:00 PM

Net Run Time, minutes 334.39 338.59 324.67

Dry Gas Meter Volume Sampled, dscf 124.260 120.922 123.303 122.828

Moisture Content of Stack Gas, % 6.52 7.05 7.26 6.943

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 6.2 6.2 6.4 6.267

Oxygen, % 12.8 12.7 12.5 12.667

Average Stack Gas Temperature, °F 233.58 236.67 237.67 235.973

Dry Volumetric Flow Rate, dry scfm 309,526.2 303,047.9 296,979.1 303,184.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 437,437.4 456,423.1 427,561.0 440,473.833

Percent Isokinetic of Sampling Rate, % 101.7 99.8 108.3 103.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 12 of 45
PSEG Sewaren Unit 4

9/3/2010

Emissions Summary

Location: Stack Exit - Method 0011

Compound: Formaldehyde

Average

RunNumber 2 3 1

Mass_mg 0.19 0.12 0.32 0.210

lb/mmBtuO2 2.00E-04 1.21E-04 3.31E-04 0.000

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1-1 1-2 1-3

Elb/hr -4.19E-01 0.00E+00 0.00E+00 -0.140

gr/dscf -2.13E-04 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 -1.03E-03 0.00E+00 0.00E+00 0.000

mg/dscm -4.87E-01 0.00E+00 0.00E+00 -0.162

ppm -4.18E-01 0.00E+00 0.00E+00 -0.139

ppm@7%O2 -1.02E+00 0.00E+00 0.00E+00 -0.340

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.000000002 0.0000000019 0.000

lb/mmBtuO2 8.39E-13 4.95E-13 4.74E-13 0.000

ng/dscm 3.94E-04 2.32E-04 2.26E-04 0.000

ng/dscm@7%O2 9.74E-04 5.75E-04 5.51E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000011 0.0000000012 0.000

lb/mmBtuO2 6.03E-13 2.72E-13 2.99E-13 0.000

ng/dscm 2.83E-04 1.27E-04 1.42E-04 0.000

ng/dscm@7%O2 7.00E-04 3.15E-04 3.46E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000013 0.0000000012 0.0000000012 0.000

lb/mmBtuO2 3.41E-13 2.97E-13 2.99E-13 0.000

ng/dscm 1.60E-04 1.39E-04 1.42E-04 0.000

ng/dscm@7%O2 3.96E-04 3.45E-04 3.46E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000011 0.0000000012 0.0000000011 0.000

lb/mmBtuO2 2.89E-13 2.97E-13 2.74E-13 0.000

ng/dscm 1.35E-04 1.39E-04 1.31E-04 0.000

ng/dscm@7%O2 3.34E-04 3.45E-04 3.19E-04 0.000

Tuesday, February 22, 2011 Page 13 of 45
PSEG Sewaren Unit 4

9/3/2010

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000125 0.00000000097 0.000000001 0.000

lb/mmBtuO2 3.28E-13 2.40E-13 2.49E-13 0.000

ng/dscm 1.54E-04 1.12E-04 1.19E-04 0.000

ng/dscm@7%O2 3.81E-04 2.78E-04 2.90E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000011 0.0000000013 0.0000000011 0.000

lb/mmBtuO2 2.89E-13 3.22E-13 2.74E-13 0.000

ng/dscm 1.35E-04 1.51E-04 1.31E-04 0.000

ng/dscm@7%O2 3.34E-04 3.74E-04 3.19E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000113 0.00000000094 0.000000001 0.000

lb/mmBtuO2 2.96E-13 2.33E-13 2.49E-13 0.000

ng/dscm 1.39E-04 1.09E-04 1.19E-04 0.000

ng/dscm@7%O2 3.44E-04 2.70E-04 2.90E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000011 0.0000000012 0.0000000011 0.000

lb/mmBtuO2 2.89E-13 2.97E-13 2.74E-13 0.000

ng/dscm 1.35E-04 1.39E-04 1.31E-04 0.000

ng/dscm@7%O2 3.34E-04 3.45E-04 3.19E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000013 0.0000000012 0.0000000013 0.000

lb/mmBtuO2 3.41E-13 2.97E-13 3.24E-13 0.000

ng/dscm 1.60E-04 1.39E-04 1.54E-04 0.000

ng/dscm@7%O2 3.96E-04 3.45E-04 3.75E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000011 0.000000001 0.0000000011 0.000

lb/mmBtuO2 2.89E-13 2.48E-13 2.74E-13 0.000

ng/dscm 1.35E-04 1.16E-04 1.31E-04 0.000

ng/dscm@7%O2 3.34E-04 2.88E-04 3.19E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000012 0.0000000012 0.0000000011 0.000

lb/mmBtuO2 3.15E-13 2.97E-13 2.74E-13 0.000

Tuesday, February 22, 2011 Page 14 of 45
PSEG Sewaren Unit 4

9/3/2010

ng/dscm 1.48E-04 1.39E-04 1.31E-04 0.000

ng/dscm@7%O2 3.66E-04 3.45E-04 3.19E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000037 0.0000000027 0.0000000035 0.000

lb/mmBtuO2 9.71E-13 6.69E-13 8.73E-13 0.000

ng/dscm 4.55E-04 3.13E-04 4.15E-04 0.000

ng/dscm@7%O2 1.12E-03 7.76E-04 1.01E-03 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000054 0.000000041 0.000000029 0.000

lb/mmBtuO2 1.42E-11 1.02E-11 7.23E-12 0.000

ng/dscm 6.64E-03 4.75E-03 3.44E-03 0.005

ng/dscm@7%O2 1.64E-02 1.18E-02 8.38E-03 0.012

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000027 0.00000019 0.00000012 0.000

lb/mmBtuO2 7.08E-11 4.70E-11 2.99E-11 0.000

ng/dscm 3.32E-02 2.20E-02 1.42E-02 0.023

ng/dscm@7%O2 8.21E-02 5.45E-02 3.46E-02 0.057

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000022 0.000000015 0.000000011 0.000

lb/mmBtuO2 5.77E-12 3.71E-12 2.74E-12 0.000

ng/dscm 2.71E-03 1.74E-03 1.31E-03 0.002

ng/dscm@7%O2 6.70E-03 4.31E-03 3.19E-03 0.005

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.0000000011 0.0000000079 0.000

lb/mmBtuO2 4.72E-12 2.72E-13 1.97E-12 0.000

ng/dscm 2.21E-03 1.27E-04 9.38E-04 0.001

ng/dscm@7%O2 5.46E-03 3.15E-04 2.29E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000081 0.00000054 0.00000034 0.000

lb/mmBtuO2 2.12E-10 1.34E-10 8.48E-11 0.000

ng/dscm 9.97E-02 6.25E-02 4.04E-02 0.068

ng/dscm@7%O2 2.46E-01 1.55E-01 9.84E-02 0.166

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Tuesday, February 22, 2011 Page 15 of 45
PSEG Sewaren Unit 4

9/3/2010

Mass_mg 0.000000012 0.0000000083 0.0000000052 0.000

lb/mmBtuO2 3.15E-12 2.06E-12 1.30E-12 0.000

ng/dscm 1.48E-03 9.61E-04 6.17E-04 0.001

ng/dscm@7%O2 3.66E-03 2.38E-03 1.50E-03 0.003

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000011 0.0000000011 0.0000000012 0.000

lb/mmBtuO2 2.89E-13 2.72E-13 2.99E-13 0.000

ng/dscm 1.35E-04 1.27E-04 1.42E-04 0.000

ng/dscm@7%O2 3.34E-04 3.15E-04 3.46E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000024 0.0000000016 0.0000000021 0.000

lb/mmBtuO2 6.30E-13 3.96E-13 5.24E-13 0.000

ng/dscm 2.95E-04 1.85E-04 2.49E-04 0.000

ng/dscm@7%O2 7.29E-04 4.59E-04 6.07E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000014 0.0000000012 0.0000000011 0.000

lb/mmBtuO2 3.67E-13 2.97E-13 2.74E-13 0.000

ng/dscm 1.72E-04 1.39E-04 1.31E-04 0.000

ng/dscm@7%O2 4.25E-04 3.45E-04 3.19E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000004 0.0000000031 0.0000000034 0.000

lb/mmBtuO2 1.05E-12 7.68E-13 8.48E-13 0.000

ng/dscm 4.92E-04 3.59E-04 4.04E-04 0.000

ng/dscm@7%O2 1.22E-03 8.90E-04 9.84E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000029 0.0000000034 0.0000000031 0.000

lb/mmBtuO2 7.61E-13 8.42E-13 7.73E-13 0.000

ng/dscm 3.57E-04 3.94E-04 3.68E-04 0.000

ng/dscm@7%O2 8.83E-04 9.77E-04 8.97E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.000000003 0.0000000052 0.0000000029 0.000

lb/mmBtuO2 7.87E-13 1.29E-12 7.23E-13 0.000

ng/dscm 3.69E-04 6.02E-04 3.44E-04 0.000

ng/dscm@7%O2 9.12E-04 1.49E-03 8.38E-04 0.001

Tuesday, February 22, 2011 Page 16 of 45
PSEG Sewaren Unit 4

9/3/2010

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000065 0.000000028 0.000000019 0.000

lb/mmBtuO2 1.70E-11 6.93E-12 4.74E-12 0.000

ng/dscm 8.00E-03 3.24E-03 2.26E-03 0.005

ng/dscm@7%O2 1.98E-02 8.03E-03 5.51E-03 0.011

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000034 0.0000000028 0.0000000038 0.000

lb/mmBtuO2 8.92E-13 6.93E-13 9.48E-13 0.000

ng/dscm 4.18E-04 3.24E-04 4.51E-04 0.000

ng/dscm@7%O2 1.03E-03 8.03E-04 1.10E-03 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.000000012 0.0000000125 0.000

lb/mmBtuO2 4.72E-12 2.97E-12 3.12E-12 0.000

ng/dscm 2.21E-03 1.39E-03 1.48E-03 0.002

ng/dscm@7%O2 5.46E-03 3.45E-03 3.61E-03 0.004

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000039 0.000000003 0.0000000034 0.000

lb/mmBtuO2 1.02E-12 7.43E-13 8.48E-13 0.000

ng/dscm 4.80E-04 3.47E-04 4.04E-04 0.000

ng/dscm@7%O2 1.19E-03 8.60E-04 9.84E-04 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.000000002 0.0000000019 0.000

lb/mmBtuO2 8.39E-13 4.95E-13 4.74E-13 0.000

ng/dscm 3.94E-04 2.32E-04 2.26E-04 0.000

ng/dscm@7%O2 9.74E-04 5.75E-04 5.51E-04 0.001

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000026 0.0000000013 0.0000000014 0.000

lb/mmBtuO2 6.82E-13 3.22E-13 3.49E-13 0.000

ng/dscm 3.20E-04 1.51E-04 1.66E-04 0.000

ng/dscm@7%O2 7.91E-04 3.74E-04 4.04E-04 0.001

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000078 0.0000000055 0.0000000052 0.000

lb/mmBtuO2 2.05E-12 1.36E-12 1.30E-12 0.000

Tuesday, February 22, 2011 Page 17 of 45
PSEG Sewaren Unit 4

9/3/2010

ng/dscm 9.60E-04 6.37E-04 6.17E-04 0.001

ng/dscm@7%O2 2.37E-03 1.58E-03 1.50E-03 0.002

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000024 0.000000001 0.0000000011 0.000

lb/mmBtuO2 6.30E-13 2.48E-13 2.74E-13 0.000

ng/dscm 2.95E-04 1.16E-04 1.31E-04 0.000

ng/dscm@7%O2 7.29E-04 2.88E-04 3.19E-04 0.000

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000021 0.0000000011 0.0000000011 0.000

lb/mmBtuO2 5.51E-13 2.72E-13 2.74E-13 0.000

ng/dscm 2.58E-04 1.27E-04 1.31E-04 0.000

ng/dscm@7%O2 6.38E-04 3.15E-04 3.19E-04 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000024 0.000000005 0.0000000044 0.000

lb/mmBtuO2 6.30E-13 1.24E-12 1.10E-12 0.000

ng/dscm 2.95E-04 5.79E-04 5.22E-04 0.000

ng/dscm@7%O2 7.29E-04 1.44E-03 1.27E-03 0.001

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000046 0.0000000022 0.0000000016 0.000

lb/mmBtuO2 1.21E-12 5.45E-13 3.99E-13 0.000

ng/dscm 5.66E-04 2.55E-04 1.90E-04 0.000

ng/dscm@7%O2 1.40E-03 6.32E-04 4.63E-04 0.001

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000108 0.0000000069 0.0000000077 0.000

lb/mmBtuO2 2.83E-12 1.71E-12 1.92E-12 0.000

ng/dscm 1.33E-03 7.99E-04 9.14E-04 0.001

ng/dscm@7%O2 3.29E-03 1.98E-03 2.23E-03 0.003

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000000357 0.0000000228 0.0000000223 0.000

lb/mmBtuO2 9.36E-12 5.65E-12 5.56E-12 0.000

ng/dscm 4.39E-03 2.64E-03 2.65E-03 0.003

ng/dscm@7%O2 1.09E-02 6.55E-03 6.46E-03 0.008

Compound: Total Furans

Average

RunNumber 1 2 3

Tuesday, February 22, 2011 Page 18 of 45
PSEG Sewaren Unit 4

9/3/2010

Mass_mg 0.0000000221 0.0000000172 0.000000018 0.000

lb/mmBtuO2 5.80E-12 4.26E-12 4.49E-12 0.000

ng/dscm 2.72E-03 1.99E-03 2.14E-03 0.002

ng/dscm@7%O2 6.72E-03 4.93E-03 5.21E-03 0.006

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1-1 1-2 1-3

Elb/hr 9.43E-02 0.00E+00 0.00E+00 0.031

gr/dscf 4.79E-05 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 2.32E-04 0.00E+00 0.00E+00 0.000

mg/dscm 1.10E-01 0.00E+00 0.00E+00 0.037

ppm 5.98E-02 0.00E+00 0.00E+00 0.020

ppm@7%O2 1.46E-01 0.00E+00 0.00E+00 0.049

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 3 1 2

Mass_mg 0.45 0.4 0.47 0.440

Elb/hr 3.62E-01 3.20E-01 3.89E-01 0.357

lb/mmBtuO2 9.25E-04 8.33E-04 9.33E-04 0.001

mg/dscm 4.40E-01 3.84E-01 4.39E-01 0.421

mg/dscm@7%O2 1.07E+00 9.65E-01 1.08E+00 1.038

Compound: Hydrogen Fluoride

Average

RunNumber 3 1 2

Mass_mg 0.11 0.11 0.11 0.110

Elb/hr 8.85E-02 8.79E-02 9.10E-02 0.089

lb/mmBtuO2 2.26E-04 2.29E-04 2.18E-04 0.000

mg/dscm 1.08E-01 1.06E-01 1.03E-01 0.106

mg/dscm@7%O2 2.63E-01 2.66E-01 2.54E-01 0.261

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 3 2 4

Mass_mg 0.30723 0.3012 0.3152 0.308

Elb/hr 5.79E-02 5.67E-02 5.97E-02 0.058

lb/mmBtuO2 7.25E-05 7.17E-05 7.34E-05 0.000

mg/dscm 4.96E-02 4.85E-02 5.14E-02 0.050

mg/dscm@7%O2 8.41E-02 8.32E-02 8.51E-02 0.084

Compound: Arsenic

Average

RunNumber 3 2 4

Mass_mg 0.008 0.00828 0.00844 0.008

Elb/hr 1.51E-03 1.56E-03 1.60E-03 0.002

lb/mmBtuO2 1.89E-06 1.97E-06 1.97E-06 0.000

mg/dscm 1.29E-03 1.33E-03 1.38E-03 0.001

Tuesday, February 22, 2011 Page 19 of 45
PSEG Sewaren Unit 4

9/3/2010

mg/dscm@7%O2 2.19E-03 2.28E-03 2.28E-03 0.002

Compound: Beryllium

Average

RunNumber 3 2 4

Mass_mg 0.0021 0.00196 0.00209 0.002

Elb/hr 3.96E-04 3.69E-04 3.96E-04 0.000

lb/mmBtuO2 4.95E-07 4.67E-07 4.87E-07 0.000

mg/dscm 3.39E-04 3.15E-04 3.41E-04 0.000

mg/dscm@7%O2 5.75E-04 5.41E-04 5.64E-04 0.001

Compound: Cadmium

Average

RunNumber 3 2 4

Mass_mg 0.000324 0.000324 0.000306 0.000

Elb/hr 6.10E-05 6.10E-05 5.80E-05 0.000

lb/mmBtuO2 7.64E-08 7.71E-08 7.13E-08 0.000

mg/dscm 5.23E-05 5.21E-05 4.99E-05 0.000

mg/dscm@7%O2 8.87E-05 8.94E-05 8.26E-05 0.000

Compound: Chromium

Average

RunNumber 3 4 2

Mass_mg 0.00543 0.00571 0.00762 0.006

Elb/hr 1.02E-03 1.08E-03 1.43E-03 0.001

lb/mmBtuO2 1.28E-06 1.33E-06 1.81E-06 0.000

mg/dscm 8.76E-04 9.32E-04 1.23E-03 0.001

mg/dscm@7%O2 1.48E-03 1.54E-03 2.11E-03 0.002

Compound: Cobalt

Average

RunNumber 3 2 4

Mass_mg 0.1510825 0.15506 0.15705 0.154

Elb/hr 2.85E-02 2.92E-02 2.98E-02 0.029

lb/mmBtuO2 3.56E-05 3.69E-05 3.66E-05 0.000

mg/dscm 2.44E-02 2.49E-02 2.56E-02 0.025

mg/dscm@7%O2 4.14E-02 4.27E-02 4.24E-02 0.042

Compound: Filterable Particulate

Average

RunNumber 3 2 4

Mass_mg 44.1 46.3 58.6 49.667

Elb/hr 8.31E+00 8.71E+00 1.11E+01 9.373

lb/mmBtuO2 1.04E-02 1.10E-02 1.36E-02 0.012

mg/dscm 7.12E+00 7.45E+00 9.56E+00 8.043

mg/dscm@7%O2 1.21E+01 1.28E+01 1.58E+01 13.567

Compound: Lead

Average

RunNumber 3 4 2

Mass_mg 0.02327 0.02413 0.02412 0.024

Elb/hr 4.38E-03 4.57E-03 4.54E-03 0.004

lb/mmBtuO2 5.49E-06 5.62E-06 5.74E-06 0.000

mg/dscm 3.75E-03 3.94E-03 3.88E-03 0.004

Tuesday, February 22, 2011 Page 20 of 45
PSEG Sewaren Unit 4

9/3/2010

mg/dscm@7%O2 6.36E-03 6.52E-03 6.66E-03 0.007

Compound: Manganese

Average

RunNumber 3 4 2

Mass_mg 0.2554 0.2636 0.2617 0.260

Elb/hr 4.81E-02 5.00E-02 4.93E-02 0.049

lb/mmBtuO2 6.03E-05 6.14E-05 6.23E-05 0.000

mg/dscm 4.12E-02 4.30E-02 4.21E-02 0.042

mg/dscm@7%O2 6.98E-02 7.12E-02 7.22E-02 0.071

Compound: Nickel

Average

RunNumber 3 4 2

Mass_mg 2.5917 2.6743 2.6611175 2.642

Elb/hr 4.88E-01 5.07E-01 5.01E-01 0.499

lb/mmBtuO2 6.11E-04 6.23E-04 6.34E-04 0.001

mg/dscm 4.18E-01 4.36E-01 4.28E-01 0.427

mg/dscm@7%O2 7.09E-01 7.21E-01 7.34E-01 0.721

Compound: Selenium

Average

RunNumber 3 4 2

Mass_mg 0.0039 0.0047 0.0045 0.004

Elb/hr 7.35E-04 8.91E-04 8.47E-04 0.001

lb/mmBtuO2 9.20E-07 1.09E-06 1.07E-06 0.000

mg/dscm 6.29E-04 7.67E-04 7.24E-04 0.001

mg/dscm@7%O2 1.07E-03 1.27E-03 1.24E-03 0.001

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1-1 1-2 1-3

Elb/hr 1.16E+02 1.12E+02 1.15E+02 114.333

lb/mmBtuO2 2.90E-01 2.91E-01 2.88E-01 0.290

mg/dscm 1.37E+02 1.38E+02 1.36E+02 137.000

mg/dscm@7%O2 3.35E+02 3.39E+02 3.34E+02 336.000

ppm 5.16E+01 5.17E+01 5.11E+01 51.467

ppm@7%O2 1.26E+02 1.27E+02 1.25E+02 126.000

Location: Stack Exit - Method 6C 3

Compound: Sulfur Dioxide

Average

Run 3-1 3-2 3-3

Elb/hr 1.06E+02 1.18E+02 1.12E+02 112.000

lb/mmBtuO2 2.77E-01 2.83E-01 2.86E-01 0.282

mg/dscm 1.28E+02 1.33E+02 1.36E+02 132.333

mg/dscm@7%O2 3.22E+02 3.28E+02 3.31E+02 327.000

ppm 4.80E+01 4.99E+01 5.12E+01 49.700

ppm@7%O2 1.21E+02 1.23E+02 1.25E+02 123.000

Location: Stack Exit - Method 7E

Tuesday, February 22, 2011 Page 21 of 45
PSEG Sewaren Unit 4

9/3/2010

Process Run Data

Compound: Nitrogen oxides (NOx)

Average

Run 3-1 3-2 3-3

Elb/hr 7.90E+01 8.65E+01 8.04E+01 81.967

lb/mmBtuO2 2.08E-01 2.12E-01 2.06E-01 0.209

mg/dscm 9.59E+01 1.00E+02 9.82E+01 98.033

mg/dscm@7%O2 2.41E+02 2.46E+02 2.39E+02 242.000

ppm 5.02E+01 5.23E+01 5.14E+01 51.300

ppm@7%O2 1.26E+02 1.29E+02 1.25E+02 126.667

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 3 2 4

Mass_mg 37.5 35.6 38.5 37.200

lb/mmBtuO2 1.60E-02 1.50E-02 1.57E-02 0.016

Compound: Filterable PM2.5

Average

RunNumber 3 2 4

Mass_mg 35.2 31.4 35 33.867

lb/mmBtuO2 1.50E-02 1.32E-02 1.43E-02 0.014

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 3 2 4

Mass_mg 2.4 1.5 3.4 2.433

lb/mmBtuO2 1.02E-03 6.31E-04 1.39E-03 0.001

Compound: Organic Condensible Particulate

Average

RunNumber 3 2 4

Mass_mg 0.9 1.5 0.8 1.067

lb/mmBtuO2 3.84E-04 6.31E-04 3.27E-04 0.000

Compound: Total Particulate

Average

RunNumber 3 2 4

Mass_mg 40.8 38.6 42.7 40.700

lb/mmBtuO2 1.74E-02 1.62E-02 1.75E-02 0.017

Compound: Total PM2.5

Average

RunNumber 3 2 4

Mass_mg 38.5 34.4 39.2 37.367

lb/mmBtuO2 1.64E-02 1.45E-02 1.60E-02 0.016

Tuesday, February 22, 2011 Page 22 of 45
PSEG Sewaren Unit 4

9/3/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 1 M0010 

Start 6/4/2010 

7:06 End 6/4/2010 

9:22

0

1 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 1 M0010 

Start 6/4/2010 

7:06 End 6/4/2010 

9:22

0

1 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 1 M0010 

Start 6/4/2010 

7:06 End 6/4/2010 

9:22

0

2 Fuel Oil Firing Rate 2562 gal/hr SEW4 Group 1 

Run 2 M25A 

(TOC as propane) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

2 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 2 M25A 

(TOC as propane) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

2 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 2 M25A 

(TOC as propane) 

Start 6/4/2010 

10:10 End 

6/4/2010 

12:14SEW4 

Group 1 Run 2 

M25A (TOC as 

propane) Start 

6/4/2010 10:10 

End 6/4/2010 

12:14

0

3 Fuel Oil Firing Rate 2542 gal/hr SEW4 Group 2 

Run 2 M23 Start 

6/2/2010 23:16 

End 6/3/2010 7:40

0

3 Unit Gross Electrical Output 30 Mwe SEW4 Group 2 

Run 2 M23 Start 

6/2/2010 23:16 

End 6/3/2010 7:40

0

Tuesday, February 22, 2011 Page 23 of 45
PSEG Sewaren Unit 4

9/3/2010

3 Unit Net Electric Generation 28 MWh SEW4 Group 2 

Run 2 M23 Start 

6/2/2010 23:16 

End 6/3/2010 7:40

0

4 Fuel Oil Firing Rate 4980 gal/hr SEW4 Group 4 

Run 2 M29 Start 

6/2/2010 9:25 End 

6/2/2010 15:19

0

4 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 2 M29 Start 

6/2/2010 9:25 End 

6/2/2010 15:19

0

4 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 2 M29 Start 

6/2/2010 9:25 End 

6/2/2010 15:19

0

5 Fuel Oil Firing Rate 4978 gal/hr SEW4 Group 4 

Run 3 

OTM027/028 Start 

6/2/2010 16:10 

End 6/2/2010 

22:04

0

5 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 3 

OTM027/028 Start 

6/2/2010 16:10 

End 6/2/2010 

22:04

0

5 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 3 

OTM027/028 Start 

6/2/2010 16:10 

End 6/2/2010 

22:04

0

6 Fuel Oil Firing Rate 4978 gal/hr SEW4 Group 4 

Run 3 M30B Start 

6/2/2010 15:49 

End 6/2/2010 

21:49

0

6 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 3 M30B Start 

6/2/2010 15:49 

End 6/2/2010 

21:49

0

6 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 3 M30B Start 

6/2/2010 15:49 

End 6/2/2010 

21:49

0

Tuesday, February 22, 2011 Page 24 of 45
PSEG Sewaren Unit 4

9/3/2010

7 Fuel Oil Firing Rate 5056 gal/hr SEW4 Group 4 

Run 4 M29 Start 

6/3/2010 9:00 End 

6/3/2010 14:49

0

7 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 4 M29 Start 

6/3/2010 9:00 End 

6/3/2010 14:49

0

7 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 4 M29 Start 

6/3/2010 9:00 End 

6/3/2010 14:49

0

8 Fuel Oil Firing Rate 5056 gal/hr SEW4 Group 4 

Run 4 

OTM027/028 Start 

6/3/2010 9:00 End 

6/3/2010 14:40

0

8 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 4 

OTM027/028 Start 

6/3/2010 9:00 End 

6/3/2010 14:40

0

8 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 4 

OTM027/028 Start 

6/3/2010 9:00 End 

6/3/2010 14:40

0

9 Fuel Oil Firing Rate 5055 gal/hr SEW4 Group 4 

Run 4 M30B Start 

6/3/2010 8:58 End 

6/3/2010 14:58

0

9 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 4 M30B Start 

6/3/2010 8:58 End 

6/3/2010 14:58

0

9 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 4 M30B Start 

6/3/2010 8:58 End 

6/3/2010 14:58

0

10 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 1 M0011 

Start 6/4/2010 

7:06 End 6/4/2010 

9:22

0

10 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 1 M0011 

Start 6/4/2010 

7:06 End 6/4/2010 

9:22

0

Tuesday, February 22, 2011 Page 25 of 45
PSEG Sewaren Unit 4

9/3/2010

10 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 1 M0011 

Start 6/4/2010 

7:06 End 6/4/2010 

9:22

0

11 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Runs 1-4 M0031 

Start 6/4/2010 

7:10 End 6/4/2010 

9:17

0

11 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Runs 1-4 M0031 

Start 6/4/2010 

7:10 End 6/4/2010 

9:17

0

11 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Runs 1-4 M0031 

Start 6/4/2010 

7:10 End 6/4/2010 

9:17

0

12 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 1 M6C (SO2) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

12 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 1 M6C (SO2) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

12 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 1 M6C (SO2) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

13 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 1 M10 (CO) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

13 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 1 M10 (CO) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

13 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 1 M10 (CO) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

Tuesday, February 22, 2011 Page 26 of 45
PSEG Sewaren Unit 4

9/3/2010

14 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 1 M25A 

(TOC as propane) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

14 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 1 M25A 

(TOC as propane) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

14 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 1 M25A 

(TOC as propane) 

Start 6/4/2010 

7:15 End 6/4/2010 

9:19

0

15 Fuel Oil Firing Rate 2562 gal/hr SEW4 Group 1 

Run 2 M0010 

Start 6/4/2010 

10:08 End 

6/4/2010 12:22

0

15 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 2 M0010 

Start 6/4/2010 

10:08 End 

6/4/2010 12:22

0

15 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 2 M0010 

Start 6/4/2010 

10:08 End 

6/4/2010 12:22

0

16 Fuel Oil Firing Rate 2562 gal/hr SEW4 Group 1 

Run 2 M0011 

Start 6/4/2010 

10:08 End 

6/4/2010 12:22

0

16 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 2 M0011 

Start 6/4/2010 

10:08 End 

6/4/2010 12:22

0

16 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 2 M0011 

Start 6/4/2010 

10:08 End 

6/4/2010 12:22

0

Tuesday, February 22, 2011 Page 27 of 45
PSEG Sewaren Unit 4

9/3/2010

17 Fuel Oil Firing Rate 2562 gal/hr SEW4 Group 1 

Runs 5-8 M0031 

Start 6/4/2010 

10:09 End 

6/4/2010 12:17

0

17 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Runs 5-8 M0031 

Start 6/4/2010 

10:09 End 

6/4/2010 12:17

0

17 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Runs 5-8 M0031 

Start 6/4/2010 

10:09 End 

6/4/2010 12:17

0

18 Fuel Oil Firing Rate 2562 gal/hr SEW4 Group 1 

Run 2 M6C (SO2) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

18 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 2 M6C (SO2) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

18 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 2 M6C (SO2) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

19 Fuel Oil Firing Rate 2562 gal/hr SEW4 Group 1 

Run 2 M10 (CO) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

19 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 2 M10 (CO) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

19 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 2 M10 (CO) 

Start 6/4/2010 

10:10 End 

6/4/2010 12:14

0

20 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 3 M0010 

Start 6/4/2010 

13:18 End 

6/4/2010 15:31

0

Tuesday, February 22, 2011 Page 28 of 45
PSEG Sewaren Unit 4

9/3/2010

20 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 3 M0010 

Start 6/4/2010 

13:18 End 

6/4/2010 15:31

0

20 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 3 M0010 

Start 6/4/2010 

13:18 End 

6/4/2010 15:31

0

21 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 3 M0011 

Start 6/4/2010 

13:18 End 

6/4/2010 15:31

0

21 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 3 M0011 

Start 6/4/2010 

13:18 End 

6/4/2010 15:31

0

21 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 3 M0011 

Start 6/4/2010 

13:18 End 

6/4/2010 15:31

0

22 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Runs 9-12 M0031 

Start 6/4/2010 

13:10 End 

6/4/2010 15:31

0

22 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Runs 9-12 M0031 

Start 6/4/2010 

13:10 End 

6/4/2010 15:31

0

22 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Runs 9-12 M0031 

Start 6/4/2010 

13:10 End 

6/4/2010 15:31

0

23 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 3 M6C (SO2) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

23 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 3 M6C (SO2) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

Tuesday, February 22, 2011 Page 29 of 45
PSEG Sewaren Unit 4

9/3/2010

23 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 3 M6C (SO2) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

24 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 3 M10 (CO) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

24 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 3 M10 (CO) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

24 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 3 M10 (CO) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

25 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 3 M25A 

(TOC as propane) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

25 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 3 M25A 

(TOC as propane) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

25 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 3 M25A 

(TOC as propane) 

Start 6/4/2010 

13:19 End 

6/4/2010 15:23

0

26 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 1 M18 (CH4) 

Start 6/4/2010 

16:26 End 

6/4/2010 16:30

0

26 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 1 M18 (CH4) 

Start 6/4/2010 

16:26 End 

6/4/2010 16:30

0

Tuesday, February 22, 2011 Page 30 of 45
PSEG Sewaren Unit 4

9/3/2010

26 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 1 M18 (CH4) 

Start 6/4/2010 

16:26 End 

6/4/2010 16:30

0

27 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 2 M18 (CH4) 

Start 6/4/2010 

16:33 End 

6/4/2010 16:36

0

27 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 2 M18 (CH4) 

Start 6/4/2010 

16:33 End 

6/4/2010 16:36

0

27 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 2 M18 (CH4) 

Start 6/4/2010 

16:33 End 

6/4/2010 16:36

0

28 Fuel Oil Firing Rate 2561 gal/hr SEW4 Group 1 

Run 3 M18 (CH4) 

Start 6/4/2010 

16:39 End 

6/4/2010 16:43

0

28 Unit Gross Electrical Output 30 Mwe SEW4 Group 1 

Run 3 M18 (CH4) 

Start 6/4/2010 

16:39 End 

6/4/2010 16:43

0

28 Unit Net Electric Generation 28 MWh SEW4 Group 1 

Run 3 M18 (CH4) 

Start 6/4/2010 

16:39 End 

6/4/2010 16:43

0

29 Fuel Oil Firing Rate 2564 gal/hr SEW4 Group 2 

Run 1 M23 Start 

6/1/2010 21:45 

End 6/2/2010 6:00

0

29 Unit Gross Electrical Output 30 Mwe SEW4 Group 2 

Run 1 M23 Start 

6/1/2010 21:45 

End 6/2/2010 6:00

0

29 Unit Net Electric Generation 28 MWh SEW4 Group 2 

Run 1 M23 Start 

6/1/2010 21:45 

End 6/2/2010 6:00

0

30 Fuel Oil Firing Rate 2552 gal/hr SEW4 Group 2 

Run 3 M23 Start 

6/3/2010 18:12 

End 6/4/2010 2:27

0

Tuesday, February 22, 2011 Page 31 of 45
PSEG Sewaren Unit 4

9/3/2010

30 Unit Gross Electrical Output 30 Mwe SEW4 Group 2 

Run 3 M23 Start 

6/3/2010 18:12 

End 6/4/2010 2:27

0

30 Unit Net Electric Generation 28 MWh SEW4 Group 2 

Run 3 M23 Start 

6/3/2010 18:12 

End 6/4/2010 2:27

0

31 Fuel Oil Firing Rate 2564 gal/hr SEW4 Group 3 

Run 1 M26A Start 

6/1/2010 9:12 End 

6/1/2010 10:34

0

31 Unit Gross Electrical Output 30 Mwe SEW4 Group 3 

Run 1 M26A Start 

6/1/2010 9:12 End 

6/1/2010 10:34

0

31 Unit Net Electric Generation 28 MWh SEW4 Group 3 

Run 1 M26A Start 

6/1/2010 9:12 End 

6/1/2010 10:34

0

32 Fuel Oil Firing Rate 2564 gal/hr SEW4 Group 3 

Run 1 M6C (SO2) 

Start 6/1/2010 

9:14 End 6/1/2010 

10:20

0

32 Unit Gross Electrical Output 30 Mwe SEW4 Group 3 

Run 1 M6C (SO2) 

Start 6/1/2010 

9:14 End 6/1/2010 

10:20

0

32 Unit Net Electric Generation 28 MWh SEW4 Group 3 

Run 1 M6C (SO2) 

Start 6/1/2010 

9:14 End 6/1/2010 

10:20

0

33 Fuel Oil Firing Rate 2564 gal/hr SEW4 Group 3 

Run 1 M7E (NOx) 

Start 6/1/2010 

9:14 End 6/1/2010 

10:20

0

33 Unit Gross Electrical Output 30 Mwe SEW4 Group 3 

Run 1 M7E (NOx) 

Start 6/1/2010 

9:14 End 6/1/2010 

10:20

0

33 Unit Net Electric Generation 28 MWh SEW4 Group 3 

Run 1 M7E (NOx) 

Start 6/1/2010 

9:14 End 6/1/2010 

10:20

0

Tuesday, February 22, 2011 Page 32 of 45
PSEG Sewaren Unit 4

9/3/2010

34 Fuel Oil Firing Rate 2563 gal/hr SEW4 Group 3 

Run 2 M26A Start 

6/1/2010 11:38 

End 6/1/2010 

12:48

0

34 Unit Gross Electrical Output 30 Mwe SEW4 Group 3 

Run 2 M26A Start 

6/1/2010 11:38 

End 6/1/2010 

12:48

0

34 Unit Net Electric Generation 28 MWh SEW4 Group 3 

Run 2 M26A Start 

6/1/2010 11:38 

End 6/1/2010 

12:48

0

35 Fuel Oil Firing Rate 2563 gal/hr SEW4 Group 3 

Run 2 M6C (SO2) 

Start 6/1/2010 

11:40 End 

6/1/2010 12:40

0

35 Unit Gross Electrical Output 30 Mwe SEW4 Group 3 

Run 2 M6C (SO2) 

Start 6/1/2010 

11:40 End 

6/1/2010 12:40

0

35 Unit Net Electric Generation 28 MWh SEW4 Group 3 

Run 2 M6C (SO2) 

Start 6/1/2010 

11:40 End 

6/1/2010 12:40

0

36 Fuel Oil Firing Rate 2563 gal/hr SEW4 Group 3 

Run 2 M7E (NOx) 

Start 6/1/2010 

11:40 End 

6/1/2010 12:40

0

36 Unit Gross Electrical Output 30 Mwe SEW4 Group 3 

Run 2 M7E (NOx) 

Start 6/1/2010 

11:40 End 

6/1/2010 12:40

0

36 Unit Net Electric Generation 28 MWh SEW4 Group 3 

Run 2 M7E (NOx) 

Start 6/1/2010 

11:40 End 

6/1/2010 12:40

0

37 Fuel Oil Firing Rate 2541 gal/hr SEW4 Group 3 

Run 3 M26A Start 

6/3/2010 15:59 

End 6/3/2010 

17:09

0

Tuesday, February 22, 2011 Page 33 of 45
PSEG Sewaren Unit 4

9/3/2010

37 Unit Gross Electrical Output 31 Mwe SEW4 Group 3 

Run 3 M26A Start 

6/3/2010 15:59 

End 6/3/2010 

17:09

0

37 Unit Net Electric Generation 29 MWh SEW4 Group 3 

Run 3 M26A Start 

6/3/2010 15:59 

End 6/3/2010 

17:09

0

38 Fuel Oil Firing Rate 2541 gal/hr SEW4 Group 3 

Run 3 M6C (SO2) 

Start 6/3/2010 

16:01 End 

6/3/2010 17:11

0

38 Unit Gross Electrical Output 31 Mwe SEW4 Group 3 

Run 3 M6C (SO2) 

Start 6/3/2010 

16:01 End 

6/3/2010 17:11

0

38 Unit Net Electric Generation 29 MWh SEW4 Group 3 

Run 3 M6C (SO2) 

Start 6/3/2010 

16:01 End 

6/3/2010 17:11

0

39 Fuel Oil Firing Rate 2541 gal/hr SEW4 Group 3 

Run 3 M7E (NOx) 

Start 6/3/2010 

16:01 End 

6/3/2010 17:11

0

39 Unit Gross Electrical Output 31 Mwe SEW4 Group 3 

Run 3 M7E (NOx) 

Start 6/3/2010 

16:01 End 

6/3/2010 17:11

0

39 Unit Net Electric Generation 29 MWh SEW4 Group 3 

Run 3 M7E (NOx) 

Start 6/3/2010 

16:01 End 

6/3/2010 17:11

0

40 Fuel Oil Firing Rate 4980 gal/hr SEW4 Group 4 

Run 2 

OTM027/028 Start 

6/2/2010 9:25 End 

6/2/2010 15:13

0

40 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 2 

OTM027/028 Start 

6/2/2010 9:25 End 

6/2/2010 15:13

0

Tuesday, February 22, 2011 Page 34 of 45
PSEG Sewaren Unit 4

9/3/2010

APCD Run Data

Process Lab Run Data

40 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 2 

OTM027/028 Start 

6/2/2010 9:25 End 

6/2/2010 15:13

0

41 Fuel Oil Firing Rate 4980 gal/hr SEW4 Group 4 

Run 2 M30B Start 

6/2/2010 9:19 End 

6/2/2010 15:19

0

41 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 2 M30B Start 

6/2/2010 9:19 End 

6/2/2010 15:19

0

41 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 2 M30B Start 

6/2/2010 9:19 End 

6/2/2010 15:19

0

42 Fuel Oil Firing Rate 4978 gal/hr SEW4 Group 4 

Run 3 M29 Start 

6/2/2010 16:10 

End 6/2/2010 

22:02

0

42 Unit Gross Electrical Output 71 Mwe SEW4 Group 4 

Run 3 M29 Start 

6/2/2010 16:10 

End 6/2/2010 

22:02

0

42 Unit Net Electric Generation 67 MWh SEW4 Group 4 

Run 3 M29 Start 

6/2/2010 16:10 

End 6/2/2010 

22:02

0

1 Heat Input Million Btus/million BTU using O2 0 0

Run Name Value UOM Comments

Target

Value

1 No control devices on Sewaren Unit 4 0 0

1 0 0

1 0 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

1 Fuel Mercury Content 0 ppm

Tuesday, February 22, 2011 Page 35 of 45
PSEG Sewaren Unit 4

9/3/2010

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

1 Fuel Nickel Content 0 ppm

1 Fuel Arsenic Content 0 ppm

1 Fuel Chromium Content 0 ppm

1 Fuel Beryllium Content 0 ppm

1 Fuel Lead Content 0 ppm

1 Fuel Manganese Content 0 ppm

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Tuesday, February 22, 2011 Page 36 of 45
PSEG Sewaren Unit 4

9/3/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:06:00 AM 10:08:00 AM 1:18:00 PM

Run Finish Time 9:22:00 AM 12:22:00 PM 3:31:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.282 0.282 0.282 0.282

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9845 0.9845 0.9845 0.985

Barometric Pressure, inches of Mercury 29.71 29.72 29.7 29.710

Average Orifice Meter Differential, inches H2O 1.29 1.23 1.34 1.287

Dry Gas Meter Volume Sampled, cubic feet 75.652 75.019 78.925 76.532

Average Dry Gas Meter Temperature, °F 82.98 88.27 91.85 87.700

Dry Gas Meter Volume Sampled, dscf 72.146 70.865 74.042 72.351

Total Moisture Liquid collected, g 87.8 87.1 96.6 90.500

Volume of Water Vapor, standard cubic feet 4.13 4.10 4.55 4.260

Moisture Content of Stack Gas, % 5.41 5.47 5.79 5.557

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9459 0.9453 0.9421 0.944

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Carbon Monoxide & Nitrogen, % 80.434 80.448 80.458 80.447

Fuel Factor 1.31 1.31 1.32

Dry Molecular Weight, lb/lb-Mole 29.30 29.30 29.30 29.300

Wet Molecular weight, lb/lb-Mole 28.69 28.68 28.65 28.673

Flue Gas Static Pressure, inches of H2O -0.18 -0.18 -0.18 -0.180

Absolute Flue Gas Pressure, inches of Mercury 29.70 29.71 29.69 29.700

Average Stack Gas Temperature, °F 214.33 219.04 222.92 218.763

Average Velocity Head, inches of H2O 0.2596215632

99566

0.246412717

488421

0.267932805

226047

0.258

Average Stack Gas Velocity, feet/second 32.55 31.82 33.31 32.560

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 229,463.3 222,694.8 230,858.0 227,672.033

Actual Wet Volumetric Flue Gas Flow Rate, acfm 312,112.8 305,113.1 319,400.3 312,208.733

Percent Isokinetic of Sampling Rate, % 96.5 97.7 98.5 97.567

Percent Excess Air, % 253.2 253.7 253.8 253.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 37 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 10

Average

Run Number 1-1 1-2 1-3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:15:00 AM 10:10:00 AM 1:19:00 PM

Run Finish Time 9:19:00 AM 12:14:00 PM 3:23:00 PM

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Fuel Factor 1.31 1.31 1.32

Dry Volumetric Flow Rate, dry scfm 229604.2 222554.8 230858 227,672.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.41 5.47 5.79 5.557

Analyzer Make Thermo 

Scientific

Thermo 

Scientific

Thermo 

Scientific

Analyzer Model 48i 48i 48i

Analyzer Serial Number CMO0846005

2

CMO846005

2

CMO846005

2

Operating Range 100.1 100.1 100.1 100.100

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 111 111 111 111.000

Calibration Pre Zero Cylinder ID Nitrogen-CO Nitrogen-CO Nitrogen-CO

Calibration Pre Zero Cylinder Instrument Response 0.512 0.341 0.097 0.317

Calibration Pre Zero Cylinder Bias 0.54 0.36 0.12 0.340

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM055217-

CO-Mid

ALM055217

-CO-Mid

ALM055217-

CO-Mid

Calibration Pre High Cylinder Instrument Response 51.147 50.83 50.195 50.724

Calibration Pre High Cylinder Bias -0.02 -0.34 -0.98 -0.447

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-CO Nitrogen-CO Nitrogen-CO

Calibration Post Zero Cylinder Instrument Response 0.341 0.097 0.195 0.211

Calibration Post Zero Cylinder Bias 0.36 0.12 0.22 0.233

Calibration Post Zero Cylinder Drift 0.18 0.24 0.1 0.173

Calibration Post High Cylinder ID ALM055217-

CO-Mid

ALM055217

-CO-Mid

ALM055217-

CO-Mid

Calibration Post High Cylinder Instrument Response 50.83 50.195 50.585 50.537

Calibration Post High Cylinder Bias -0.34 -0.98 -0.59 -0.637

Calibration Post High Cylinder Drift 0.32 0.64 0.39 0.450

Cavg 0.011 -0.074 -0.128 -0.064

Cavg Units ppmvd ppmvd ppmvd

Cgas -0.4183 0 0 -0.139

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 38 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 6/1/2010 6/2/2010 6/3/2010

Run Start Time 6:00:00 AM 7:40:00 AM 2:27:00 AM

Run Finish Time 9:45:00 PM 11:16:00 PM 6:12:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.282 0.282 0.283 0.282

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9982 0.992

Barometric Pressure, inches of Mercury 29.56 29.64 29.56 29.587

Average Orifice Meter Differential, inches H2O 1.16 1.31 1.27 1.247

Dry Gas Meter Volume Sampled, cubic feet 301.914 318.941 317.552 312.802

Average Dry Gas Meter Temperature, °F 83.67 82.17 97.38 87.740

Dry Gas Meter Volume Sampled, dscf 287.092 305.056 297.596 296.581

Total Moisture Liquid collected, g 345.4 356.7 331.8 344.633

Volume of Water Vapor, standard cubic feet 16.26 16.79 15.62 16.223

Moisture Content of Stack Gas, % 5.36 5.22 4.99 5.190

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9464 0.9478 0.9501 0.948

Carbon Dioxide, % 4.225 4.249 4.276 4.250

Oxygen, % 15.277 15.294 15.195 15.255

Carbon Monoxide & Nitrogen, % 80.498 80.457 80.529 80.495

Fuel Factor 1.33 1.32 1.33

Dry Molecular Weight, lb/lb-Mole 29.29 29.29 29.29 29.290

Wet Molecular weight, lb/lb-Mole 28.68 28.70 28.73 28.703

Flue Gas Static Pressure, inches of H2O -0.18 -0.26 -0.18 -0.207

Absolute Flue Gas Pressure, inches of Mercury 29.55 29.62 29.55 29.573

Average Stack Gas Temperature, °F 213.63 217.63 303.25 244.837

Average Velocity Head, inches of H2O 0.2452290255

67998

0.273827716

646396

0.264511847

603664

0.261

Average Stack Gas Velocity, feet/second 31.70 33.55 35.02 33.423

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 222,691.2 235,198.5 217,976.2 225,288.633

Actual Wet Volumetric Flue Gas Flow Rate, acfm 303,962.4 321,701.6 335,797.0 320,487.000

Percent Isokinetic of Sampling Rate, % 99.0 99.6 104.1 100.900

Percent Excess Air, % 255.7 257.2 250.6 254.500

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 39 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 25A

Average

Run Number 1-1 1-2 1-3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:15:00 AM 10:10:00 AM 1:19:00 PM

Run Finish Time 9:19:00 AM 12:14:00 PM 3:23:00 PM

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Fuel Factor 1.31 1.31 1.32

Dry Volumetric Flow Rate, dry scfm 229604.2 222554.8 230858 227,672.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.41 5.47 5.79 5.557

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 51C 51C 51C

Analyzer Serial Number 0327202203 0327202203 0327202203 327,202,203

.000

Operating Range 10 10 10 10.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 252 252 252 252.000

Calibration Pre Zero Cylinder ID NitrogenC3H8NitrogenC3H8NitrogenC3H8

Calibration Pre Zero Cylinder Instrument Response -0.046 0.026 -0.124 -0.048

Calibration Pre Zero Cylinder Bias -0.12 0.6 -0.9 -0.140

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ZZZ00000-

THC-Low

ZZZ00000-

THC-Low

ZZZ00000-

THC-Low

Calibration Pre High Cylinder Instrument Response 2.888 2.807 2.939 2.878

Calibration Pre High Cylinder Bias 0.3 -0.51 0.81 0.200

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID NitrogenC3H8NitrogenC3H8NitrogenC3H8

Calibration Post Zero Cylinder Instrument Response 0.026 -0.124 0.046 -0.017

Calibration Post Zero Cylinder Bias 0.6 -0.9 0.8 0.167

Calibration Post Zero Cylinder Drift 0.72 1.5 1.7 1.307

Calibration Post High Cylinder ID ZZZ00000-

THC-Low

ZZZ00000-

THC-Low

ZZZ00000-

THC-Low

Calibration Post High Cylinder Instrument Response 2.807 2.939 2.978 2.908

Calibration Post High Cylinder Bias -0.51 0.81 1.2 0.500

Calibration Post High Cylinder Drift 0.81 1.32 0.39 0.840

Cavg 0.047 -0.952 -0.229 -0.378

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.0598 0 0 0.020

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 40 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 6/1/2010 6/1/2010 6/3/2010

Run Start Time 9:12:00 AM 11:38:00 AM 3:59:00 PM

Run Finish Time 10:34:00 AM 12:48:00 PM 5:09:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.282 0.282 0.283 0.282

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988

Barometric Pressure, inches of Mercury 29.81 29.66 29.56 29.677

Average Orifice Meter Differential, inches H2O 1.26 1.42 1.23 1.303

Dry Gas Meter Volume Sampled, cubic feet 39.171 40.613 39.058 39.614

Average Dry Gas Meter Temperature, °F 95.54 97.96 99.38 97.627

Dry Gas Meter Volume Sampled, dscf 36.769 37.781 36.104 36.885

Total Moisture Liquid collected, g 65.3 67.2 62.1 64.867

Volume of Water Vapor, standard cubic feet 3.07 3.16 2.92 3.050

Moisture Content of Stack Gas, % 7.71 7.72 7.48 7.637

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9229 0.9228 0.9252 0.924

Carbon Dioxide, % 4.096 4.266 4.346 4.236

Oxygen, % 15.37 15.257 15.192 15.273

Carbon Monoxide & Nitrogen, % 80.534 80.477 80.462 80.491

Fuel Factor 1.35 1.32 1.31

Dry Molecular Weight, lb/lb-Mole 29.27 29.29 29.30 29.287

Wet Molecular weight, lb/lb-Mole 28.40 28.42 28.45 28.423

Flue Gas Static Pressure, inches of H2O -0.18 -0.18 -0.17 -0.177

Absolute Flue Gas Pressure, inches of Mercury 29.80 29.65 29.55 29.667

Average Stack Gas Temperature, °F 229.83 218.21 229.42 225.820

Average Velocity Head, inches of H2O 0.2579668651

45581

0.288376472

855786

0.253085386

527665

0.266

Average Stack Gas Velocity, feet/second 32.93 34.60 32.72 33.417

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 222,153.7 236,198.5 219,561.1 225,971.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 315,756.5 331,769.7 313,742.9 320,423.033

Percent Isokinetic of Sampling Rate, % 101.6 98.2 100.3 100.033

Percent Excess Air, % 260.9 254.8 251.1 255.600

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 41 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 29 

Average

Run Number 2 3 4

Test Date 6/2/2010 6/2/2010 6/3/2010

Run Start Time 9:25:00 AM 4:10:00 PM 9:00:00 AM

Run Finish Time 3:19:00 PM 10:02:00 PM 2:49:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 336 336 336

Nozzle Diameter, inches 0.248 0.248 0.248 0.248

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988

Barometric Pressure, inches of Mercury 29.74 29.685 29.595 29.673

Average Orifice Meter Differential, inches H2O 1.44 1.42 1.44 1.433

Dry Gas Meter Volume Sampled, cubic feet 234.964 233.282 233.814 234.020

Average Dry Gas Meter Temperature, °F 96.96 93.67 99.50 96.710

Dry Gas Meter Volume Sampled, dscf 219.573 218.882 216.450 218.302

Total Moisture Liquid collected, g 354.4 339.7 353.4 349.167

Volume of Water Vapor, standard cubic feet 16.68 15.99 16.63 16.433

Moisture Content of Stack Gas, % 7.06 6.81 7.13 7.000

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9294 0.9319 0.9287 0.930

Carbon Dioxide, % 6.2 6.2 6.4 6.267

Oxygen, % 12.8 12.7 12.5 12.667

Carbon Monoxide & Nitrogen, % 81 81.1 81.1 81.067

Fuel Factor 1.31 1.32 1.31

Dry Molecular Weight, lb/lb-Mole 29.50 29.50 29.52 29.507

Wet Molecular weight, lb/lb-Mole 28.69 28.72 28.70 28.703

Flue Gas Static Pressure, inches of H2O 0.17 0.17 0.17 0.170

Absolute Flue Gas Pressure, inches of Mercury 29.75 29.70 29.61 29.687

Average Stack Gas Temperature, °F 240.75 242.54 243.63 242.307

Average Velocity Head, inches of H2O 0.5171538774

00968

0.514597162

209225

0.515246218

941005

0.516

Average Stack Gas Velocity, feet/second 46.79 46.75 46.90 46.813

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 312,401.1 311,651.5 310,152.5 311,401.700

Actual Wet Volumetric Flue Gas Flow Rate, acfm 448,656.2 448,272.7 449,711.0 448,879.967

Percent Isokinetic of Sampling Rate, % 99.7 99.6 99.0 99.433

Percent Excess Air, % 149.1 145.8 140.3 145.067

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 42 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 6C

Average

Run Number 1-1 1-2 1-3

Test Date 6/4/2010 6/4/2010 6/4/2010

Run Start Time 7:15:00 AM 10:10:00 AM 1:19:00 PM

Run Finish Time 9:14:00 AM 12:14:00 PM 3:23:00 PM

Carbon Dioxide, % 4.344 4.318 4.305 4.322

Oxygen, % 15.222 15.234 15.237 15.231

Fuel Factor 1.31 1.31 1.32

Dry Volumetric Flow Rate, dry scfm 224759.9 217795.8 226006.6 222,854.100

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.41 5.47 5.79 5.557

Analyzer Make Ametek Ametek Ametek

Analyzer Model 921 CE 921CE 921CE

Analyzer Serial Number AE-921-6434 AE-921-

6434

AE-921-6434

Operating Range 205.9 205.9 205.9 205.900

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 411 411 411 411.000

Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Pre Zero Cylinder Instrument Response 2.262 2.066 2.164 2.164

Calibration Pre Zero Cylinder Bias 1.34 1.25 1.29 1.293

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM045659-

SO2-Mid

ALM045659

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Pre High Cylinder Instrument Response 96.027 94.748 96.125 95.633

Calibration Pre High Cylinder Bias -1.72 -2.34 -1.67 -1.910

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Post Zero Cylinder Instrument Response 2.066 2.164 2.164 2.131

Calibration Post Zero Cylinder Bias 1.25 1.29 1.29 1.277

Calibration Post Zero Cylinder Drift 9.0000000000

0001E-02

0.04 0 0.043

Calibration Post High Cylinder ID ALM045659-

SO2-Mid

ALM045659

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Post High Cylinder Instrument Response 94.748 96.125 95.928 95.600

Calibration Post High Cylinder Bias -2.34 -1.67 -1.77 -1.927

Calibration Post High Cylinder Drift 0.62 0.67 0.1 0.463

Cavg 50.734 50.834 50.621 50.730

Cavg Units ppmvd ppmvd ppmvd

Cgas 51.5796 51.6835 51.1093 51.457

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 43 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 6C 3

Average

Run Number 3-1 3-2 3-3

Test Date 6/1/2010 6/1/2010 6/3/2010

Run Start Time 9:14:00 AM 11:40:00 AM 4:01:00 PM

Run Finish Time 10:20:00 AM 12:40:00 PM 5:11:00 PM

Carbon Dioxide, % 4.096 4.266 4.346 4.236

Oxygen, % 15.37 15.257 15.192 15.273

Fuel Factor 1.35 1.32 1.31

Dry Volumetric Flow Rate, dry scfm 222153.7 235993.7 219494 225,880.467

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 7.71 7.72 7.78 7.737

Analyzer Make Ametek Ametek Ametek

Analyzer Model 921CE 921CE 921CE

Analyzer Serial Number AE-921-6434 AD-921-

6434

AE-921-6434

Operating Range 201 201 412 271.333

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 3 3 61 22.333

Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Pre Zero Cylinder Instrument Response -0.097 2.447 1.911 1.420

Calibration Pre Zero Cylinder Bias 0.1 1.37 0.66 0.710

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM000000-

SO2-Mid

ALM000000

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Pre High Cylinder Instrument Response 93.886 94.963 95.757 94.869

Calibration Pre High Cylinder Bias -2.97 -2.44 -1.17 -2.193

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Post Zero Cylinder Instrument Response 0.783 3.23 3.319 2.444

Calibration Post Zero Cylinder Bias 0.54 1.76 1 1.100

Calibration Post Zero Cylinder Drift 0.44 0.39 0.34 0.390

Calibration Post High Cylinder ID ALM000000-

SO2-Mid

ALM000000

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Post High Cylinder Instrument Response 95.844 91.047 97.467 94.786

Calibration Post High Cylinder Bias -2 -4.38 -0.76 -2.380

Calibration Post High Cylinder Drift 0.97 1.94 0.41 1.107

Cavg 45.742 47.872 51.188 48.267

Cavg Units ppmvd ppmvd ppmvd

Cgas 48.0301 49.9448 51.1583 49.711

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 44 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - Method 7E

Average

Run Number 3-1 3-2 3-3

Test Date 6/1/2010 6/1/2010 6/3/2010

Run Start Time 9:14:00 AM 11:40:00 AM 4:01:00 PM

Run Finish Time 10:20:00 AM 12:40:00 PM 5:11:00 PM

Carbon Dioxide, % 4.096 4.266 4.346 4.236

Oxygen, % 15.37 15.257 15.192 15.273

Fuel Factor 1.35 1.32 1.31

Dry Volumetric Flow Rate, dry scfm 219995.4 231026.6 218381 223,134.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 7.71 7.72 7.78 7.737

Analyzer Make ThermoElectro

n

Thermo 

Electron

Thermo 

Electron

Analyzer Model 42CLS 42 CLS 42CLS

Analyzer Serial Number 0328202427 0328202427 0328202427 328,202,427

.000

Operating Range 201 201 198 200.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 41 41 51 44.333

Calibration Pre Zero Cylinder ID Nitrogen-NOx NitrogenNOxNitrogenNOx

Calibration Pre Zero Cylinder Instrument Response 0.098 0.294 0.679 0.357

Calibration Pre Zero Cylinder Bias 0 0.1 0.29 0.130

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID AAL021731-

NOx-Mid

AAL021731-

NOx-Mid

ALM045659-

NOx-Mid

Calibration Pre High Cylinder Instrument Response 94.611 95.641 92.702 94.318

Calibration Pre High Cylinder Bias -1.42 -0.9 -1.45 -1.257

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-NOx NitrogenNOxNitrogenNOx

Calibration Post Zero Cylinder Instrument Response 0.294 0.49 0.679 0.488

Calibration Post Zero Cylinder Bias 0.1 0.2 0.29 0.197

Calibration Post Zero Cylinder Drift 0.1 0.1 0 0.067

Calibration Post High Cylinder ID AAL021731-

NOx-Mid

AAL021731-

NOx-Mid

ALM045659-

NOx-Mid

Calibration Post High Cylinder Instrument Response 87.593 96.623 92.653 92.290

Calibration Post High Cylinder Bias -4.91 -0.41 -1.47 -2.263

Calibration Post High Cylinder Drift 2.33 0.49 0.02 0.947

Cavg 45.88 50.541 48.316 48.246

Cavg Units ppmvd ppmvd ppmvd

Cgas 50.1536 52.2756 51.366 51.265

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 45 of 45
PSEG Sewaren Unit 4

9/3/2010

Location Stack Exit - OTM - 27/28

Average

Run Number 2 3 4

Test Date 6/2/2010 6/2/2010 6/3/2010

Run Start Time 9:25:00 AM 4:10:00 PM 9:00:00 AM

Run Finish Time 3:13:00 PM 10:04:00 PM 2:40:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 334.39 338.59 324.67

Nozzle Diameter, inches 0.186 0.186 0.186 0.186

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9845 0.9845 0.9845 0.985

Barometric Pressure, inches of Mercury 29.74 28.185 29.595 29.173

Average Orifice Meter Differential, inches H2O 0.46 0.48 0.48 0.473

Dry Gas Meter Volume Sampled, cubic feet 131.852 136.902 131.968 133.574

Average Dry Gas Meter Temperature, °F 88.88 95.08 90.96 91.640

Dry Gas Meter Volume Sampled, dscf 124.260 120.922 123.303 122.828

Total Moisture Liquid collected, g 183.9 194.9 205.1 194.633

Volume of Water Vapor, standard cubic feet 8.66 9.17 9.65 9.160

Moisture Content of Stack Gas, % 6.52 7.05 7.26 6.943

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9348 0.9295 0.9274 0.931

Carbon Dioxide, % 6.2 6.2 6.4 6.267

Oxygen, % 12.8 12.7 12.5 12.667

Carbon Monoxide & Nitrogen, % 81 81.1 81.1 81.067

Fuel Factor 1.31 1.32 1.31

Dry Molecular Weight, lb/lb-Mole 29.50 29.50 29.52 29.507

Wet Molecular weight, lb/lb-Mole 28.75 28.69 28.68 28.707

Flue Gas Static Pressure, inches of H2O 0.17 0.17 0.17 0.170

Absolute Flue Gas Pressure, inches of Mercury 29.75 28.20 29.61 29.187

Average Stack Gas Temperature, °F 233.58 236.67 237.67 235.973

Average Velocity Head, inches of H2O 0.4976509775

03412

0.510276432

24862

0.469207798

192785

0.492

Average Stack Gas Velocity, feet/second 45.62 47.60 44.59 45.937

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 309,526.2 303,047.9 296,979.1 303,184.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 437,437.4 456,423.1 427,561.0 440,473.833

Percent Isokinetic of Sampling Rate, % 101.7 99.8 108.3 103.267

Percent Excess Air, % 149.1 145.8 140.3 145.067

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 46 of 45