# Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

-down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg+2

# , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

# , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

-downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

# 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

# (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

# This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

# and , HgP, and Hg+2 

# . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

-down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

# 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also

# EIA

Facility Code Facility Name Boiler ID

60 Wh elan Energy

Center WE C1

# Control Device Configuraton

Listed (by

boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR

# Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR

# EIA

Facility Code Facility Name Boiler ID 60 Wh elan Energy

Center WE C1

Run Number Test Start Date Test Start Time

# Measured Value (ppm)

Test End Date Test End Time

# Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) CO Emission Test Results

# Test Method Comments lb/mmBtu ppmdv @ 7% O 2 

# Calculated Emission Rate

# Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%)

# Flue Gas O2

# (%) Flue Gas Flow Rate (dscfm) Flue Gas CO2

# (%)

# Fuel Input Rate Fuel Type

Flue Gas Temperature (F) Fuel #1

# Units of Measure Measurement Method Fuel Input Rate Fuel #1

# Fuel Type Units of Measure Measurement Method Fuel #2

# Fuel Input Rate Fuel Type Units of Measure Fuel #3

# Measurement Method Fuel Input Rate Fuel Type Fuel #4

# Units of Measure Measurement Method Fuel #4 Other Supporting InformationEIA Facility Code Facility Name Boiler ID 60 Whelan Energy Center WEC1

1 3/23/2010 8:12 2 3/23/2010 11:24 3 3/23/2010 14:22 Test End Date Run Number Test Start Date Test Start Time Test End TimeMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments lb/mmBtu ppmdv @ 7% O2 Dry U.S. EPA Method 0011 Dry U.S. EPA Method 0011 Dry U.S. EPA Method 0011

Formaldehyde Emission Test Results Calculated Emission RateFuel Input Rate Fuel

Type Units of

Measure Flue Gas Temperature (F) Fuel #1 Total Heat Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas Flow

Rate (dscfm) Steam Output (1000 lb/hr)Measurement Method Fuel Input

Rate Fuel

Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel

Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel

Type Units of

Measure Measurement

Method Other Supporting Information Fuel #2 Fuel #3 Fuel #4EIA Facility Code Facility Name Boiler ID 60 Whelan Energy Center WEC1

Measured Value (ppm) Basis (Wet or Dry)

1 3/23/2010 7:59 3/23/2010 9:59 <0.353 Dry 2 3/23/2010 10:40 3/23/2010 12:35 <0.347 Dry 3 3/23/2010 13:33 3/23/2010 15:34 <0.205 Dry Test End Date Run Number Test Start Date Test Start Time Test End Time Methane Emission Test ResultsTest Method Used Data Flag (ADL, BDL, DDL) Test Method Comments lb/mmBtu ppmdv @ 7% O2

U.S. EPA Method 18 DLL Average of results that were both ADL and BDL. <0.000203 <0.327 U.S. EPA Method 18 DLL Average of results that were both ADL and BDL. <0.000204 <0.325 U.S. EPA Method 18 DLL Average of results that were both ADL and BDL. <0.000205 <0.192 Methane Emission Test Results Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel

Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel

Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel

Type Units of

Measure

11.3 13.4 5.91 212357 321 12.5 13.5 6.03 211051 325 11.4 13.5 6.07 208414 324

Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Flue Gas Moisture (%) Flue Gas CO2(%) Flue Gas Temperat ure (F) Fuel #1 Fuel #2 Fuel #3Measurement Method Fuel

Input Rate Fuel

Type Units of

Measure Measurement

Method Fuel #4 Other Supporting Information

# EIA

Facility Code Facility Name Boiler ID 60 Wh elan Energy

Center WE C1

Test End Date Run Number Test Start Date Test Start Time

# Measured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time SO2

# Emission Test Results

# Data Flag (ADL,

BDL, DDL) Test Method

Comments lb/mmBtu ppmdv @ 7% O 2 

# Calculated Emission Rate Steam Output (1000 lb/hr)

# Fuel Input Rate Fuel Type Flue Gas O 2

# (%) Flue Gas

Flow Rate (dscfm) Total Heat Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO 2

# (%) Flue Gas Temperature (F) Fuel #1

# Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Fuel #1 Fuel #2 Fuel #3

# Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Fuel #3

# Other Supporting InformationEIA Facility Code Facility Name Boiler ID 60 Wh elan Energy Center WE C1 Please note QA/QC documentation starting in Column "AI"

Measured Value (μg/dscm) Basis (Wet or Dry)

1 3/24/2010 9:18 3/24/2010 11:18 10 Dry 2 3/24/2010 13:10 3/24/2010 15:10 10.7 Dry 3 3/25/2010 8:01 3/25/2010 10:01 9.08 Dry Run Number Test Start Date Test Start Time Test End Time Test End Date Total Vapor Phase Mercury Emission Test ResultsPlease note QA/QC documentation starting in Column "AI"

Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments (lb/mmBtu)

U.S. EPA Method 30BADL 0.00000887 11.8 13.8 6.16 197956 327 U.S. EPA Method 30BADL 0.00000945 11.8 13.8 6.16 197944 327 U.S. EPA Method 30BADL 0.00000798 11.9 13.9 6.08 200131 315 Flue Gas Temperature (F) Total Vapor Phase Mercury Emission Test Results Flue Gas Moisture (%) Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm)Fuel Input Rate Fuel

Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel

Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel

Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel

Type Fuel #1 Fuel #2 Fuel #3 Fuel #4QA/QC Documentation

Units of Measure Measurement

Method Trap ID Section 1 Mass (ng) Section 2

Mass (ng) Total

Mass (ng) Initial

Spike (ng) Total NonSpike (ng) Sample

Volume (dscm) Volume

Difference (%) Volume Diff.

Limit

56771 1090 0.4 1090.4 0 1090.4 120.4 0.0033 59754 1120 0.3 1120.3 0 1120.3 120.2 0.0017 56751 1020 0.7 1020.7 0 1020.7 123.6 0.03 ≤20% of field recovery test Trap #1 Other Supporting Information Fuel #4Breaktrough (%) Breaktrough

Limit Concentration

(μg/dscm) Trap ID Section 1 Mass Section 2

Mass Total

Mass Initial

Spike Total NonSpike Sample

Volume Volume

Difference (%) Volume Diff. Limit Breaktrough

(%)

0.036697248 0.009056478 59661 1590 0.9 1590.9 500 1090.9 120 0 0.056603774 0.026785714 0.0093203 59657 1660 0 1660 500 1160 120.4 0.0033 0 0.068627451 0.008258091 59670 1490 0.6 1490.6 500 990.6 121.2 0.01 0.040268456 #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0!

≤10% of Section 1 Hg mass for Hg conc. >1

μg/dscm: or ≤ 20% of Section ≤20% of field recovery test Trap #2Breaktrough Limit Concentration

(μg/dscm) Abs. diff. RD (%) Limit C rec R (%) by Run Ravg(%) Limit

0.009090833 3.44E-05 0.189311 4.3 100.8 0.009634551 0.000314 1.657897 4.72 108.8 0.008173267 8.48E-05 0.516228 4.19 99.5 #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! #DIV/0! ≥ 10 % RD mass for Hg conc. >1 μg/dscm: or

≤20% RD or ≤0.2 μg/dscm abs.diff. for Hg conc. ≤1 ≤10% of Section 1 Hg mass for Hg conc. >1

μg/dscm: or ≤ 20% of Section 1 for Hg conc. ≤1 Average Recovery, between 85 and 115% Measured Spike Recovery ( R )

103.033333 Paired Trap Agreement (RD)

# EIA

Facility Code Facility Name Boiler ID 60 Wh elan Energy

Center WE C1

Run Number Test Start Date Test Start Time

# Measured Hg 0

# Value (μg/dscm) Measured Hg +2

# Value (μg/dscm) Test End Time Test End Date

# Measured Hg P

# Value

(μg/dscm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Total Vapor Phase Mercury Emission Test Results

# Test Method

Comments Total Mercury (lb/mmBtu) Steam Output

(1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO 2

# (%)

# Fuel Input Rate Fuel Type Units of Measure Measurement

Method Flue Gas O 2

# (%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1

# Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3

# Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Other Supporting Information Fuel #4EIA Facility Code Facility Name Boiler ID 60 Whelan Energy Center WE C1

Speciated Volatile Organic HAP Emission Data

Benzene 1 3/23/2010 8:12 AM 3/23/2010 Benzene 2 3/23/2010 11:24 AM 3/23/2010 Benzene 3 3/23/2010 2:22 PM 3/23/2010 Methyl bromide 1 3/23/2010 8:12 AM 3/23/2010 Methyl bromide 2 3/23/2010 11:24 AM 3/23/2010 Methyl bromide 3 3/23/2010 2:22 PM 3/23/2010 Carbon disulfide 1 3/23/2010 8:12 AM 3/23/2010 Carbon disulfide 2 3/23/2010 11:24 AM 3/23/2010 Carbon disulfide 3 3/23/2010 2:22 PM 3/23/2010 Carbon tetrachloride 1 3/23/2010 8:12 AM 3/23/2010 Carbon tetrachloride 2 3/23/2010 11:24 AM 3/23/2010 Carbon tetrachloride 3 3/23/2010 2:22 PM 3/23/2010 Chloroform 1 3/23/2010 8:12 AM 3/23/2010 Chloroform 2 3/23/2010 11:24 AM 3/23/2010 Chloroform 3 3/23/2010 2:22 PM 3/23/2010 Methyl chloride 1 3/23/2010 8:12 AM 3/23/2010 Methyl chloride 2 3/23/2010 11:24 AM 3/23/2010 Methyl chloride 3 3/23/2010 2:22 PM 3/23/2010 Ethylbenzene 1 3/23/2010 8:12 AM 3/23/2010 Ethylbenzene 2 3/23/2010 11:24 AM 3/23/2010 Ethylbenzene 3 3/23/2010 2:22 PM 3/23/2010 Methylene chloride 1 3/23/2010 8:12 AM 3/23/2010 Methylene chloride 2 3/23/2010 11:24 AM 3/23/2010 Methylene chloride 3 3/23/2010 2:22 PM 3/23/2010 Trichloroethylene 1 3/23/2010 8:12 AM 3/23/2010 Trichloroethylene 2 3/23/2010 11:24 AM 3/23/2010 Trichloroethylene 3 3/23/2010 2:22 PM 3/23/2010 Toluene 1 3/23/2010 8:12 AM 3/23/2010 Toluene 2 3/23/2010 11:24 AM 3/23/2010 Toluene 3 3/23/2010 2:22 PM 3/23/2010 m-Xylene 1 3/23/2010 8:12 AM 3/23/2010 m-Xylene 2 3/23/2010 11:24 AM 3/23/2010 m-Xylene 3 3/23/2010 2:22 PM 3/23/2010 o-Xylene 1 3/23/2010 8:12 AM 3/23/2010 o-Xylene 2 3/23/2010 11:24 AM 3/23/2010 o-Xylene 3 3/23/2010 2:22 PM 3/23/2010 1,1,2-Trichloroethane 1 3/23/2010 8:12 AM 3/23/2010

Compound (use drop down to define for as many rows as

needed) Run Number Test Start Date Test Start Time Test End DateFootnotes: * Front half fraction contains filter, cyclone, and cartridge ** Back half fraction contains condensate, solvent, impingers

Measured Value (μg/m3) Basis Test Method Used Data Flag (ADL, BDL, DDL) Front Half Mass (μg) Back Half Mass (μg)

10:41 AM <1.43 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <1.07 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <1.15 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <2.44 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <1.46 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <3.60 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <4.64 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <1.30 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <2.79 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <0.171 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <0.201 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM 0.184 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <0.169 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <0.152 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <0.146 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <3.61 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <2.11 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <4.14 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <0.134 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <0.136 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <0.139 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <346 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <585 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <718 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <0.189 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <0.155 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <0.787 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <1.28 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <1.49 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <0.500 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <0.236 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <0.239 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <0.244 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM <0.132 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 1:35 PM <0.140 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 4:26 PM <0.143 Dry U.S. EPA Method 0031 with SW -846 Method 8260B DLL 10:41 AM [<1.08] Dry U.S. EPA Method 0031 with SW -846 Method 8260B BDL Test End TimeTotal Mass (μg) Test Method Comments lb/mmBtu μg/dscm @ 7% O2 <0.110 .025, .021, .021, .027, .0046, [<.0035], [<.0035], [.0035] <1.23E-06 <1.32 11.3 <0.0606 .02, .013, .016, [<.0035], [<.0035], [<.0035] <9.28E-07 <1.00 12.5 <0.0636 <9.97E-07 <1.07 11.4 <0.188 <2.10E-06 <2.26 11.3 <0.0826 .013, .021, .0095, .018, .0093, [<..0059] <1.27E-06 <1.36 12.5 <0.199 <3.13E-06 <3.37 11.4 <0.358 .016, .042, .0064, .11, .0056, [<.0019], [<.0019], .012 <3.99E-06 <4.30 11.3 <0.0734 .0047, .0089, .023, .0033, [<.0019], [<.0019] <1.12E-06 <1.21 12.5 <0.155 .0044, .0048, .024, .012, [<.0019], [<.0019] <2.43E-06 <2.62 11.4 <0.0132 .0016, [<.0012], .0017, .0016, [<.0012], [<.0012], [<.0012], [<.0012] <1.47E-07 <0.159 11.3 <0.0114 .0018, .0019, .0018, [<.0012], [<.0012], [<.0012] <1.75E-07 <0.188 12.5 <0.0102 .0018, [<.0012], .0013, .0012, [<.0012], [<.0012] <1.60E-07 <0.172 11.4 <0.0130 .0014, .0032, .0014, [<.0011], [<.0011], [<.0011],[<.0011], [<.0011] <1.45E-07 <0.157 11.3 <0.00863 [<.0011], [<.0011], .0016, [<.0011], [<.0011], [<.0011] <1.32E-07 <0.142 12.5 <0.00812 <1.27E-07 <0.137 11.4 <0.279 <3.11E-06 <3.35 11.3 <0.120 <1.83E-06 <1.98 12.5 <0.230 <3.60E-06 <3.88 11.4 <0.0103 .0013, [<.001], [<.001], [<.001], .0013, [<.001], [<.001], [<.001] <1.15E-07 <0.124 11.3 <0.00770 <1.18E-07 <0.127 12.5 <0.00769 <1.21E-07 <0.130 11.4 <26.7 <2.98E-04 <321 11.3 <33.1 <5.07E-04 <547 12.5 <39.8 <6.25E-04 <673 11.4 <0.0146 [<.0011], .0043, .0015, [<.0011], [<.0011], [<.0011], [<.0011], [<.0011] <1.63E-07 <0.175 11.3 <0.00876 <1.34E-07 <0.145 12.5 <0.0437 [<.0011], [<.0011], .036, [<.0011], [<.0011], [<.0011] <6.85E-07 <0.738 11.4 <0.0986 <1.10E-06 <1.19 11.3 <0.0846 <1.30E-06 <1.40 12.5 <0.0277 <4.35E-07 0.468 11.4 <0.0182 .0021, [<.002], [<.002], [<.002], .0026, [<.002], [<.002], [<.002] <2.03E-07 <0.219 11.3 <0.0135 m-xylene and p-xylene <2.07E-07 <0.223 12.5 <0.0135 are together as one result <2.12E-07 <0.229 11.4 <0.0102 [<.001], [<.001], [<.001], [<.001], .0012, [<.001], [<.001], [<.001] <1.13E-07 <0.122 11.3 <0.00795 <1.22E-07 <0.131 12.5 <0.00795 <1.25E-07 <0.134 11.4 [<0.0834] [<9.30E-07] [<1.00] 11.3 Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%) Calculated Emission RateFuel Input Rate Fuel Type Units of Measure

13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321 13.5 6.03 211051 325 13.5 6.07 208414 324 13.4 5.91 212357 321

Flue Gas O2(%) Flue Gas Flow Rate (scfm) Flue Gas Temperature (F) Fuel #1 Flue Gas CO2(%)Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Fuel #2 Fuel #3Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel #4 Other Supporting Information Fuel #3EIA Facility Code Facility Name Boiler ID 60 Whelan Energy Center WE C1

Speciated Semi-Volatile Organic HAP Emission Data

Acenaphthene 1 3/23/2010 8:12 AM 3/23/2010 Acenaphthene 2 3/23/2010 11:24 AM 3/23/2010 Acenaphthene 3 3/23/2010 2:22 PM 3/23/2010 Acenaphthylene 1 3/23/2010 8:12 AM 3/23/2010 Acenaphthylene 2 3/23/2010 11:24 AM 3/23/2010 Acenaphthylene 3 3/23/2010 2:22 PM 3/23/2010 Acetophenone 1 3/23/2010 8:12 AM 3/23/2010 Acetophenone 2 3/23/2010 11:24 AM 3/23/2010 Acetophenone 3 3/23/2010 2:22 PM 3/23/2010 Anthracene 1 3/23/2010 8:12 AM 3/23/2010 Anthracene 2 3/23/2010 11:24 AM 3/23/2010 Anthracene 3 3/23/2010 2:22 PM 3/23/2010 Benzo(a)anthracene 1 3/23/2010 8:12 AM 3/23/2010 Benzo(a)anthracene 2 3/23/2010 11:24 AM 3/23/2010 Benzo(a)anthracene 3 3/23/2010 2:22 PM 3/23/2010 Benzo(b)fluoranthene 1 3/23/2010 8:12 AM 3/23/2010 Benzo(b)fluoranthene 2 3/23/2010 11:24 AM 3/23/2010 Benzo(b)fluoranthene 3 3/23/2010 2:22 PM 3/23/2010 Benzo(k)fluoranthene 1 3/23/2010 8:12 AM 3/23/2010 Benzo(k)fluoranthene 2 3/23/2010 11:24 AM 3/23/2010 Benzo(k)fluoranthene 3 3/23/2010 2:22 PM 3/23/2010 Benzoic acid 1 3/23/2010 8:12 AM 3/23/2010 Benzoic acid 2 3/23/2010 11:24 AM 3/23/2010 Benzoic acid 3 3/23/2010 2:22 PM 3/23/2010 Benzo(g,h,i)perylene 1 3/23/2010 8:12 AM 3/23/2010 Benzo(g,h,i)perylene 2 3/23/2010 11:24 AM 3/23/2010 Benzo(g,h,i)perylene 3 3/23/2010 2:22 PM 3/23/2010 Benzo(a)pyrene 1 3/23/2010 8:12 AM 3/23/2010 Benzo(a)pyrene 2 3/23/2010 11:24 AM 3/23/2010 Benzo(a)pyrene 3 3/23/2010 2:22 PM 3/23/2010 Benzo(e)pyrene 1 3/23/2010 8:12 AM 3/23/2010 Benzo(e)pyrene 2 3/23/2010 11:24 AM 3/23/2010 Benzo(e)pyrene 3 3/23/2010 2:22 PM 3/23/2010 Bis(2-ethylhexyl) phthalate 1 3/23/2010 8:12 AM 3/23/2010 Bis(2-ethylhexyl) phthalate 2 3/23/2010 11:24 AM 3/23/2010 Bis(2-ethylhexyl) phthalate 3 3/23/2010 2:22 PM 3/23/2010 Chrysene 1 3/23/2010 8:12 AM 3/23/2010 Chrysene 2 3/23/2010 11:24 AM 3/23/2010 Chrysene 3 3/23/2010 2:22 PM 3/23/2010 Dibenzo(a,h)anthracene 1 3/23/2010 8:12 AM 3/23/2010 Dibenzo(a,h)anthracene 2 3/23/2010 11:24 AM 3/23/2010 Dibenzo(a,h)anthracene 3 3/23/2010 2:22 PM 3/23/2010 Fluoranthene 1 3/23/2010 8:12 AM 3/23/2010 Fluoranthene 2 3/23/2010 11:24 AM 3/23/2010 Fluoranthene 3 3/23/2010 2:22 PM 3/23/2010 Fluorene 1 3/23/2010 8:12 AM 3/23/2010 Fluorene 2 3/23/2010 11:24 AM 3/23/2010 Fluorene 3 3/23/2010 2:22 PM 3/23/2010 Indeno(1,2,3-cd)pyrene 1 3/23/2010 8:12 AM 3/23/2010 Indeno(1,2,3-cd)pyrene 2 3/23/2010 11:24 AM 3/23/2010 Indeno(1,2,3-cd)pyrene 3 3/23/2010 2:22 PM 3/23/2010 2-Methylnaphthalene 1 3/23/2010 8:12 AM 3/23/2010 2-Methylnaphthalene 2 3/23/2010 11:24 AM 3/23/2010 2-Methylnaphthalene 3 3/23/2010 2:22 PM 3/23/2010 Naphthalene 1 3/23/2010 8:12 AM 3/23/2010 Naphthalene 2 3/23/2010 11:24 AM 3/23/2010 Naphthalene 3 3/23/2010 2:22 PM 3/23/2010 Phenanthrene 1 3/23/2010 8:12 AM 3/23/2010 Phenanthrene 2 3/23/2010 11:24 AM 3/23/2010 Phenanthrene 3 3/23/2010 2:22 PM 3/23/2010 Phenol 1 3/23/2010 8:12 AM 3/23/2010 Phenol 2 3/23/2010 11:24 AM 3/23/2010 Phenol 3 3/23/2010 2:22 PM 3/23/2010 Pyrene 1 3/23/2010 8:12 AM 3/23/2010 Pyrene 2 3/23/2010 11:24 AM 3/23/2010 Pyrene 3 3/23/2010 2:22 PM 3/23/2010 Perylene 1 3/23/2010 8:12 AM 3/23/2010

Compound (use drop down to define for as many rows as

needed) Run Number Test Start Date Test Start Time Test End DateFootnotes: * Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses ** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses *** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses

Measured Value (μg/m3) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

10:49 AM <0.00903 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.00828 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.00603 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.00370 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.00272 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM [<0.00250] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 10:49 AM <0.00338 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.00351 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.00338 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.0120 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.00478 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM [<0.00395] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 10:49 AM <0.00514 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.00381] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM <0.00489 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.00822 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.00651] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM <0.00920 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.0437 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.0436] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM <0.0477 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <64.6 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <73.7 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <61.9 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.00585 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.00518] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM <0.00681 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM 0.00402 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 1:45 PM <0.00290 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.00400 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.00615 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.00569] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM [<0.00582] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 10:49 AM <0.0110 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.0110] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM [<0.0112] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 10:49 AM 0.00938 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 1:45 PM 0.00869 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4:41 PM <0.00465 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM [<0.00393] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1:45 PM [<0.00396] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM <0.00692 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.0408 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.0279 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.0142 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.0305 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.0163 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.00785 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.00338 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM [<0.00269] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 4:41 PM <0.00577 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.0525 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.0513 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.0333 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.276 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.282 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.276 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.189 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.107 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.0489 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.00343 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.00346 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.00348 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM <0.0506 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 1:45 PM <0.0525 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 4:41 PM <0.0439 Dry U.S. EPA Method 0010 with SW-846 Method 8270C DLL 10:49 AM [<0.00308] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL Test End Time Semi-Volatile Organic HAP Emission Test Results* Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses ** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses *** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses

Front Half mass* (ng) Back Half mass* (ng) Condensate Mass*** (ng) Total Composite (ng) Test Method Comments

[<8.90] 4.2 4.8 <17.9 [<6.00] 5.5 4.8 <16.3 [<3.00] 3.8 4.8 <11.6 4.0 [<3.00] 0.3 <7.3 2.0 [<3.00] 0.4 <5.4 [<1.50] [<3.00] [<0.30] [<4.8] [<1.10] 3.6 [<2.00] <6.7 [<1.10] 3.8 [<2.00] <6.9 [<1.10] 3.4 [<2.00] <6.5 18.0 [<4.40] [<1.40] <23.8 3.6 [<4.40] [<1.40] <9.4 [<1.80] [<4.40] [<1.40] [<7.6] 4.2 [<3.00] [<3.00] <10.2 [<1.50] [<3.00] [<3.00] [<7.5] 3.4 [<3.00] [<3.00] <9.4 6.7 [<6.60] [<3.00] <16.3 [<3.20] [<6.60] [<3.00] [<12.8] 8.1 [<6.60] [<3.00] <17.7 2.7 [<82.0] [<2.00] <86.7 [<1.70] [<82.0] [<2.00] [<85.7] 7.7 [<82.0] [<2.00] <91.7 [<30000] 48000 [<50000] <128000.0 [<30000] 65000 [<50000] <145000.0 [<30000] 39000 [<50000] <119000.0 [<5.60] 4.6 1.4 <11.6 [<5.60] [<3.60] [<1.00] [<10.2] 8.5 [<3.60] [<1.00] <13.1 3.5 3.6 0.9 7.96 [<1.90] [<3.00] [<0.80] <5.7 3.9 [<3.00] [<0.80] <7.7 3.8 [<5.60] [<2.80] <12.2 [<2.80] [<5.60] [<2.80] [<11.2] [<2.80] [<5.60] [<2.80] [<11.2] 3.6 [<15.0] [<3.20] <21.8 [<3.40] [<15.0] [<3.20] [<21.6] [<3.40] [<15.0] [<3.20] [<21.6] 10.0 7.1 1.5 18.60 1.7 13.0 2.4 17.10 5.5 [<3.00] [<0.44] <8.9 [<2.60] [<3.60] [<1.60] [<7.8] [<2.60] [<3.60] [<1.60] [<7.8] 8.1 [<3.60] [<1.60] <13.3 49.0 27.0 [<4.80] <80.8 12.0 38.0 [<4.80] <54.8 7.5 15.0 [<4.80] <27.3 48.0 9.4 [<3.00] <60.4 14.0 15.0 [<3.00] <32.0 5.6 6.5 [<3.00] <15.1 2.8 1.9 [<2.00] <6.7 [<1.50] [<1.80] [<2.00] [<5.3] 7.3 [<1.80] [<2.00] <11.1 56.0 31.0 [<17.0] <104.0 44.0 40.0 [<17.0] <101.0 20.0 27.0 [<17.0] <64.0 56.0 [<460.00] [<32.0] <548.0 62.0 [<460.00] [<32.0] <554.0 39.0 [<460.00] [<32.0] <531.0 300.0 53.0 [<22.0] <375.0 100.0 88.0 [<22.0] <210.0 37.0 35.0 [<22.0] <94.0 [<2.40] 2.4 [<2.00] <6.8 [<2.40] 2.4 [<2.00] <6.8 [<2.40] 2.3 [<2.00] <6.7 [<60.0] 37.0 [<3.40] <100.4 [<60.0] 40.0 [<3.40] <103.4 [<60.0] 21.0 [<3.40] <84.4 [<1.5] [<3.0] [<1.6] [<6.1] Semi-Volatile Organic HAP Emission Test Resultslb/mmBtu μg/dscm @ 7% O2 <7.77E-09 <0.00837 12 <7.19E-09 <0.00774 12.3 <5.25E-09 <0.00565 11.6 <3.19E-09 <0.00343 12 <2.36E-09 <0.00254 12.3 [<2.17E-09] [<0.00234] 11.6 <2.91E-09 <0.00313 12 <3.04E-09 <0.00328 12.3 <2.94E-09 <0.00317 11.6 <1.03E-08 <0.0111 12 <4.15E-09 <0.00447 12.3 [<3.44E-09] [<0.00370] 11.6 <4.43E-09 <0.00477 12 [<3.31E-09] [<0.00356] 12.3 <4.25E-09 <0.00458 11.6 <7.08E-09 <0.00762 12 [<5.65E-09] [<0.00608] 12.3 <8.01E-09 <0.00863 11.6 <3.76E-08 <0.0405 12 [<3.78E-08] [<0.0407] 12.3 <4.15E-08 <0.0447 11.6 <5.56E-05 <59.9 12 <6.40E-05 <68.9 12.3 <5.38E-05 <58.0 11.6 <5.04E-09 <0.00542 12 [<4.50E-09] [<0.00485] 12.3 <5.93E-09 <0.00638 11.6 3.46E-09 <0.00372 12 <2.51E-09 <0.00271 12.3 <3.48E-09 <0.00375 11.6 <5.30E-09 <0.00571 12 [<4.94E-09] [<0.00532] 12.3 [<5.07E-09] [<0.00546] 11.6 <9.46E-09 <0.0102 12 [<9.53E-09] [<0.0103] 12.3 [<9.77E-09] [<0.0105] 11.6 8.08E-09 0.00870 12 7.54E-09 0.00812 12.3 <4.04E-09 <0.00436 11.6 [<3.39E-09] [<0.00365] 12 [<3.44E-09] [<0.00371] 12.3 <6.02E-09 <0.00648 11.6 <3.51E-08 <0.0378 12 <2.42E-08 <0.0260 12.3 <1.24E-08 <0.0133 11.6 <2.62E-08 <0.0282 12 <1.41E-08 <0.0152 12.3 <6.83E-09 <0.00736 11.6 <2.91E-09 <0.00313 12 [<2.34E-09] [<0.00252] 12.3 <5.02E-09 <0.00541 11.6 <4.52E-08 <0.0486 12 <4.45E-08 <0.0480 12.3 <2.90E-08 <0.0312 11.6 <2.38E-07 <0.256 12 <2.44E-07 <0.263 12.3 <2.40E-07 <0.259 11.6 <1.63E-07 <0.175 12 <9.26E-08 <0.0998 12.3 <4.25E-08 <0.0458 11.6 <2.95E-09 <0.00318 12 <3.00E-09 <0.00323 12.3 <3.03E-09 <0.00327 11.6 <4.36E-08 <0.0470 12 <4.56E-08 <0.0491 12.3 <3.82E-08 <0.0411 11.6 [<2.65E-09] [<0.00285] 12 Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%) Calculated Emission RateFuel Input Rate

13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321 13.5 6 202414 325 13.5 6.1 199355 324 13.4 5.9 206470 321

Flue Gas O2(%) Flue Gas Flow Rate (scfm) Flue Gas Temperature (F) Flue Gas CO2(%)Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Fuel #1 Fuel #2Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure

Fuel #2 Fuel #3Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel #4Other Supporting Information

### EIA Facility Code Facility

Name Boiler ID 60 Wh elan Energy Center WE C1

Measured Value (ppm) Basis (Wet or Dry)

1 3/24/2010 8:18 3/24/2010 12:55 [<3.89] Dry 2 3/24/2010 13:10 3/24/2010 16:31 [<4.56] Dry 3 3/25/2010 8:01 3/25/2010 13:23 [<4.69] Dry Run Number Test Start Date Test Start Time Test End Time Test End Date Hydrogen Cyanide Emission Test Results

### Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments U.S. EPA Method 26A-Mod BDL [<0.00386] 11.8 13.8 U.S. EPA Method 26A-Mod BDL [<0.00453] 11.8 13.8 U.S. EPA Method 26A-Mod BDL [<0.00460] 11.9 13.9 Hydrogen Cyanide Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas

CO2

### (%)

### Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method 6.16 197956 327 6.16 197944 327 6.08 200131 315 Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Fuel #2 Flue Gas O2

### (%)

### Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting Information Fuel #3

# EIA

Facility Code Facility Name Boiler ID

60 Wh elan Energy

Center WE C1

Run Number Test Start Date Test Start Time Test End Date

# Measured Value (ppm) Basis (Wet or Dry) Test Method Used Hydrogen Chloride Emission Test Results Test End Time

# Data Flag (ADL,

BDL, DDL) Test Method

Comments Calculated

Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO 2

# (%) Hydrogen Chloride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)

# Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Temperature (F) Fuel #1 Flue Gas O 2

# (%) Flue Gas

Flow Rate (dscfm)

# Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3

# Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting Information

# EIA

Facility Code Facility Name Boiler ID

60 Wh elan Energy

Center WE C1

Run Number Test Start Date Test Start Time Test End Date

# Measured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time Hydrogen Flouride Emission Test Results

# Data Flag (ADL,

BDL, DDL) Test Method

Comments Hydrogen Flouride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%)

# Fuel Input Rate Fuel Type Units of Measure Measurement

Method Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas CO 2

# (%) Flue Gas

O 2

# (%)

# Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3

# Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting Information

# EIA

Facility Code Facility Name Boiler ID 60 Wh elan Energy

Center WE C1

Run Number Test Start Date Test Start Time

# Measured NO (ppm)

Test End Date Test End Time

# Measured NO2

# (ppm) Basis (Wet or Dry) Test Method Used NOX

# Emission Test Results

# Data Flag (ADL, BDL, DDL) Test Method Comments (lb/mmBtu) Total NOX

# Calculated Emission Rate

# ppmdv @ 7% O 2 

# Flue Gas O 2

# (%) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO 2

# (%)

# Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1

# Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3

# Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting Information

# EIA

Facility Code Facility Name Boiler ID 60 Wh elan Energy

Center WE C1

Run Number Test Start Date Test Start Time

# Total Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter) Test End Time Test End Date

# Test Method Used Data Flag (ADL, BDL, DDL) Constisuent Emission Test Results

# Test Method Comments Fuel Input Rate Flue Gas Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Flue Gas Temperat ure (F)

# Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel #1 Fuel #2

# Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel #3 Fuel #4

# Other Supporting Information