Exhibit
10.213


 


THIRD
AMENDMENT TO


PURCHASE
AND SALE AGREEMENT


 


This
THIRD AMENDMENT TO PURCHASE AND SALE AGREEMENT (this “Amendment”) is entered into this 26th day
of February, 2015, by and between AH DURHAM APARTMENTS, LLC, a Virginia limited liability company (“Seller”),
and TRIBRIDGE RESIDENTIAL, LLC, a Georgia limited liability company (“Purchaser”).


 


WITNESSETH:


 


WHEREAS,
Seller and Purchaser entered into that certain Purchase and Sale Agreement dated as of December 1, 2014, as modified by the Agreement
Establishing Inspection Period and Inspection Date between Seller and Purchaser dated as of January 7, 2015, as further modified
First Amendment to Purchase and Sale Agreement between Seller and Purchaser dated as of February 20, 2015, and as further modified
by the Second Amendment to Purchase and Sale Agreement between Seller and Purchaser dated as of February 24, 2015 (collectively,
"Purchase Agreement") regarding certain property located at 501 Willard Street, Durham, North Carolina
27701 and commonly known as Whetstone Apartments, as more particularly described in the Purchase Agreement; and


 


WHEREAS,
Seller and Purchaser wish to further modify the Purchase Agreement as set forth below.


 


NOW
THEREFORE, for Ten Dollars ($10.00) in hand paid and other good and valuable consideration, the receipt and sufficiency of
which are hereby acknowledged, Seller and Purchaser hereby agree as follows:


 


1.           Defined
Terms. Capitalized terms contained but not defined in this Amendment shall have the meaning ascribed to such terms in the
Purchase Agreement.


 


2.           Purchase
Price. All of the text in Section 1.4 of the Purchase Agreement is hereby deleted in its entirety and the following text inserted
in lieu thereof:


 


“Seller
is to sell and Purchaser is to purchase the Property for a purchase price of THIRTY-SIX MILLION SIX HUNDRED TWENTY-FIVE THOUSAND
and NO/100 Dollars ($35,625,000.00) (the “Purchase Price”).”


 


3.           Expiration
of Inspection Period; Non-Refundability of Earnest Money. Purchaser hereby waives any and all rights Purchaser may have to
terminate the Purchase Agreement under Section 3.2 thereof, and specifically agrees and acknowledges that except if a Purchaser
Permitted Termination Event occurs or Purchaser exercises its right to terminate the Purchase Agreement pursuant to Section 4
of this Amendment, (a) the Earnest Money has become non- refundable to Purchaser, and (b) Purchaser is bound to proceed
to Closing and consummate the transaction contemplated under the Purchase Agreement.


 




     

     

    

  


4.           Parking
Deck. Purchaser is presently evaluating the possibility of adding one (1) additional level to the existing parking deck (the
“Parking Deck”) at the Property (said additional level, along with any modification to the existing
parking deck required to add the additional level, collectively, the “Parking Deck Addition”). Prior
to the expiration of the Parking Deck Feasibility Period (defined below), Purchaser shall have the right to conduct such tests,
investigations, inspections and feasibility studies as Purchaser shall require in its sole discretion to evaluate the feasibility
and cost of the Parking Deck Addition. In connection with Purchaser’s investigations, Purchaser Parties shall have the same
rights to go upon the Property to conduct these tests and inspections, and Purchaser shall have all the same obligations and is
subject to the same restrictions, including without limitation maintaining the same insurance coverages and providing the same
indemnities, as are set forth in Section 3.1 of the Purchase Agreement. Purchaser shall have until 3:00 p.m., Eastern Time on
March 4, 2015 (the period of time between the date of this Amendment and 3:00 p.m., Eastern Time on March 4, 2015 hereinafter
referred to as the "Parking Deck Feasibility Period"), to determine whether constructing the Parking Deck
Addition is feasible and the cost is acceptable to Purchaser. If Purchaser determines in its sole discretion that constructing
the Parking Deck Addition is not feasible or the cost is not otherwise acceptable, then Purchaser shall have the right to terminate
the Purchase Agreement by providing written notice to Seller on or before the expiration of the Parking Deck Feasibility Period.
If Purchaser terminates the Purchase Agreement in accordance with this provision, then the Initial Earnest Money shall be refunded
to Purchaser in accordance with Section 1.6 of the Purchase Agreement (the parties acknowledging that any such termination shall
be a "Purchaser Permitted Termination Event"), and neither party shall have any further rights or obligations under
the Purchase Agreement, except those indemnities, rights and obligations which by their express terms survive the termination
of the Purchase Agreement. Notwithstanding anything contained in Section 1.6(a) of the Purchase Agreement or any other provision
of the Purchase Agreement to the contrary, if Purchaser does not terminate the Purchase Agreement prior to the expiration of the
Parking Deck Feasibility Period, then Purchaser will deposit with the Escrow Agent the Additional Earnest Money on or before March
7, 2015.


 


5.           Additional
Work. Seller will perform certain additional work at the Property prior to Closing (in addition to the work anticipated by
the Plans and Specifications), the scope of which is set forth in Exhibit “A” attached hereto and made
a part hereof (collectively, “Additional Work”). Seller shall cause the Additional Work to be completed
in compliance with Seller’s construction covenants in Section 5.4(m) of the Purchase Agreement on or before the Closing
Date. For the avoidance of doubt, Seller's performance of the covenants set forth in this Section 5 shall constitute further conditions
precedent to Purchaser’s obligation to close on its acquisition of the Property under Section 4.6 of the Purchase Agreement.


 


6.           Additional
Inspections. As part of Purchaser’s rights under Section 5.4(m) of the Purchase Agreement, Purchaser at its sole cost
shall have the right to obtain a compliance report ("Compliance Report") from a consultant regarding those
portions of the Property which have not been assessed in the compliance reports obtained by Purchaser prior to the date of this
Amendment (said portions of the Property to include, without limitation, the so-called "Phase II" portion of the Property).


 


7.           Designated
Service Contracts. Pursuant to Section 5.4(l) of the Purchase Agreement, Purchaser has elected to assume all the Service Contracts
listed on Schedule 5.1(l) attached to the Purchase Agreement. Seller acknowledges that this Section 7 constitutes sufficient and
timely notice of Purchaser’s election under the Purchase Agreement, and the parties agree that the Service Contracts listed
on Schedule 5.1(l) attached to the Purchase Agreement shall hereafter constitute the “Designated Service Contracts”
under the Purchase Agreement.


 




    	 	2	 



     

    

  


8.           Seller’s
Leasing Activities.


 


(a)           Free
Rent Concessions. Notwithstanding any provision in the Purchase Agreement to the contrary, if the Purchaser does not terminate
the Purchase Agreement prior to the expiration of the Parking Deck Feasibility Period, then at all times after the expiration
of the Parking Deck Feasibility Period Seller shall (i) when negotiating leases with proposed new tenants at the Property, offer
up to two (2) months’ free rent concession for each new lease (to be credited at the beginning of the lease term, and not
amortized over the course of the lease) and(ii) provide, or shall cause Seller’s Leasing Agent to provide, weekly leasing
updates to Purchaser, with such supporting information as Purchaser shall reasonably request. At Purchaser’s option at any
time (but no more often than once weekly), Purchaser may direct Seller to reduce, discontinue or resume the offer of a two (2)
month free rent concessions in Seller’s leasing negotiations; provided that at all times Seller will have the right
to offer up to one (1) month free rent as provided in Section 5.4(b) of the Purchase Agreement.


 


(b)           Revision
to Apartment Lease Form. If the Purchaser does not terminate the Purchase Agreement prior to the expiration of the Parking
Deck Feasibility Period, then within five (5) days after the expiration of the Parking Deck Feasibility Period Seller shall submit
to Purchaser a proposed revision to Seller’s standard form of apartment lease for the Property, providing that no individual
unit shall be entitled to the use of more than one (1) parking space in the Parking Deck. Purchaser shall have the right to review
and approve such revision in Purchaser’s reasonable discretion. Upon Purchaser’s written approval of the revised language,
Seller shall use the revised form of lease for all new leases and Lease renewals at the Property.


 


9.           City
of Durham Redevelopment Plan. The following text shall be inserted in Section 5.1 of the Purchase Agreement as new subsection
(s) thereof:


 


“(s)
Without limitation of subsection (f) hereof, Seller represents and warrants that it has obtained or will obtain all licenses,
permits, consents and approvals required from the City of Durham, North Carolina for the construction of the Improvements, including,
but not limited to, city approval of Seller’s plan for the redevelopment of the Property, and that, to the extent needed
to construct the Improvements in compliance with all applicable laws, all previously obtained redevelopment plan approvals remain
valid and in full force and effect.”


 


10.         Closing
Date. The first sentence of Section 4.1 of the Agreement is amended by deleting the phrase “one hundred twenty (120)”
and in lieu thereof, inserting the phrase “ninety (90)”. For avoidance of doubt, the Closing Date shall be no earlier
than May 20, 2015.


 




    	 	3	 



     

    

  


11.         No
Further Modification. In the event of any inconsistency between the Purchase Agreement and this Amendment, the terms of this
Amendment shall control. Except as otherwise modified herein, all terms and conditions in the Purchase Agreement shall remain
in full force and effect.


 


12.         Miscellaneous.
This Amendment may be executed by the parties hereto individually or in combination, in one or more counterparts, each of which
shall be an original and all of which will constitute one and the same Amendment and may be delivered by facsimile or PDF via
electronic mail in a legally binding manner. This Amendment shall be governed and construed in accordance with the laws of the
State of North Carolina and shall be binding upon and shall inure to the benefit of the parties hereto and their respective heirs,
executors, administrators, personal representatives, successors and permitted assigns. Time is of the essence with respect to
the obligations of the parties set forth in this Amendment.


 


[Counterpart
signatures appear on following pages]


 




    	 	4	 



     

    

  


IN
WITNESS WHEREOF, this Amendment has been executed by the parties as of the date set forth in the preamble.


 


	 	SELLER:
	 	 
	 	AH DURHAM APARTMENTS,
    LLC
	 	 	 
	 	By:	ARMADA HOFFLER MANAGER,
    LLC,
	 	 	Its Manager
	 	 	 
	 	 	By:	/s/
    Eric L. Smith
	 	 	 	Eric
    L. Smith, Manager


 


[signatures
continue on following page]


 




    	 	5	 



     

    

  


[signatures
continued from previous page]


 


	 	PURCHASER:
	 	 
	 	TRIBRIDGE RESIDENTIAL,
    LLC, a Georgia
	 	limited liability company
	 	 	 
	 	By:	/s/ Robert
    H. West
	 	Name:	Robert H.
    West
	 	Title:	President


 




    	 	6	 



     

    

  


Exhibit
“A”


 


Scope of
Additional Work


 


Please
see attached.


 






    	 	7	 



     

    

 


 


 


	No.	 	Description
    of Items	 	Date
    first noted	 	Report
    No.	 	Status	 	Date
    Closed	 	AH
    Response
	1	 	Large
    amounts of dead and damaged plant material were observed at the west elevation.  Damage appears to have been caused by
    foot traffic.  See photo 139.	 	42040	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	2	 	Brick
    pavers at the west elevation are loose.  This may present a tripping hazard.  Landscape edging may be used to contain
    bricks in this area.  See photo 141.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	3	 	A final
    wear course needs to be installed on the asphalt drive Minor asphalt repair should be done at damaged ares prior to wear course
    installation.  See photo 133.	 	2/5/15	 	1	 	 	 	 	 	AH to address - repair complete / stripping will
    be done when weather permits
	 	 	 	 	 	 	 	 	 	 	 	 	 
	4	 	The Client
    should re-evaluate parking needs versus capacity provided.  Currently the parking deck has roughly 1 space for each apartment
    unit which may be inadequate depending on the makeup of the community.	 	2/5/15	 	1	 	 	 	 	 	NA
	 	 	 	 	 	 	 	 	 	 	 	 	 
	5	 	The top
    and bottom rail of the fence on the west elevation are out of alignment with the rest of the fence.  A fence post may
    have sunken causing this effect.  See photo 140.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	6	 	Sheet
    A13.01 calls for a “sliding entry gate” at the garage entrance. The drawings do not appear to call for a controlled
    access device on the gate.  We would expect to see this on the Parking Deck Electrical plan.  This appears to be
    a design oversight as a gate at the garage entry without a remote controlled opening/closing device would be impractical.
     No gate or controlled access device was installed at the time of our inspection.	 	2/5/15	 	1	 	 	 	 	 	AH to address - will install automatic gate
	 	 	 	 	 	 	 	 	 	 	 	 	 
	7	 	Light
    fixtures at the front entry canopy are not properly positioned as they are obstructed by downspouts.  See photo 69.	 	2/5/15	 	1	 	 	 	 	 	AH to come up with solution reasonably acceptable
    to Buyer
	 	 	 	 	 	 	 	 	 	 	 	 	 
	8	 	Storm
    drain grates in the courtyard have openings that will not prevent entry of mulch.  Clogging of the courtyard storm drain
    system may result.  See photo 109.  We recommend installation of grates with smaller openings.	 	2/5/15	 	1	 	 	 	 	 	AH to address - chickenwire to be applied under grates
	 	 	 	 	 	 	 	 	 	 	 	 	 
	9	 	Sheet
    A4.16 shows a recycling chute in the trash compactor room and a hatch in the adjacent trash room. Detail 2 on the same sheet
    shows upper level trash rooms with no recycling hatch.   This is a design oversight.  No chute is currently
    installed and no hatches are provided save that hatch at the 1st floor.  The city may have mandaory recycling ordinances
    that could impact the decision to install a chute or to abandon the issue altogether.  See photo 163 and 167.	 	2/5/15	 	1	 	 	 	 	 	As Is - per design
	 	 	 	 	 	 	 	 	 	 	 	 	 
	10	 	Plastic
    decking near the outdoor kitchen in the courtyard is cut at a taper, and the thin end of the taper is not secured.  This
    tail should be cut off.  See photo 115.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	11	 	We
    observed multiple pool drains separated by distances that satisfy the Pool and Spa Safety Act. The local pool inspector is
    the final authority on the P&SS Act, and a passing inspection certificate typically indiates his approval.  A pool
    inspection certificate / permit was not provided for our review.  See photo 120.	 	2/5/15	 	1	 	 	 	 	 	As Is - passed inspection
	 	 	 	 	 	 	 	 	 	 	 	 	 
	12	 	The property
    does not have a maintenance shop or a room dedicated to storage or maintenance tools and materials.	 	2/5/15	 	1	 	 	 	 	 	NA - Extra space in sprinkler room and other MEP
    closets
	 	 	 	 	 	 	 	 	 	 	 	 	 
	13	 	The roof
    over stair no. 2 is not flat.  The west corner dips below the plane defined by the other three corners and the roof surface
    is torqued as a result.  See photo 96.	 	2/5/15	 	1	 	 	 	 	 	As Is - sloped to provide drainage - framing and
    structure passed inspection
	 	 	 	 	 	 	 	 	 	 	 	 	 
	14	 	Some
    refrigerant and electrical lines are not caulked where they enter the building.  All such entry points should be sealed
    with silicone caulk.  See photo 82.	 	2/5/15	 	1	 	 	 	 	 	As Is
	 	 	 	 	 	 	 	 	 	 	 	 	 
	15	 	An opening
    was observed where parapet coping meets fiber-cement siding at stair 2.  The opening needs to be sealed.  See photo
    97.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	16	 	The relationship
    of scuppers and conductor heads differs dimensionally from the design shown in detail 1/A9.05.  However, we believe the
    installation is satisfactory.  See photo 99.	 	2/5/15	 	1	 	 	 	 	 	As Is
	 	 	 	 	 	 	 	 	 	 	 	 	 
	17	 	Several
    screws and other pieces of metal debris were found on the roof.  These may cause damage to the roof if stepped on.  The
    roof should be carefully cleared of all debris.  See photo 103.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	18	 	Brick
    masonry repair was done on the west elevation near grade for an unknown reason.  The brick needs to be cleaned in this
    area.  See photo 138.	 	2/5/15	 	1	 	 	 	 	 	AH to address


 




     

     

    

  


 


 


	No.	 	Description
    of Items	 	Date
    first noted	 	Report
    No.	 	Status	 	Date
    Closed	 	AH
    Response
	19	 	An opening
    was found in the brick rowlock course outside the balcony at unit 117.  This needs to be caulked. See photo 173.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	20	 	Window
    openings are not restricted to 4".  The omission of window opeing limiters presents a fall hazard and is a violation
    of the 2012 IBC.  Regardless of code applicablility, this is a preventable safety hazard and exposes the building owner
    to liability. See photo 170.	 	2/5/15	 	1	 	 	 	 	 	AH to come up with solution reasonably acceptable
    to Buyer
	 	 	 	 	 	 	 	 	 	 	 	 	 
	21	 	Detail
    3/A10.01 calls for a peep hole in unit entry doors at handicap units between 43 and 51 inches above finished floor.  No
    such peep holes exist.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	22	 	A steel
    brick lintel needs to be painted at an exterior door on the east elevation.  See photo 62.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	23	 	Blistered
    paint was found on the underside of the main entry canopy.  A water leak above may have caused this.  See photo
    70.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	24	 	The painted
    finish on concrete balcony door sills at the ground level on the west elevation is damaged in several locations.  This
    appears to be caused by loading materials through the sliding doors.  See photo 137.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	25	 	Condensing
    units on roof are to be positioned on wood sleepers wrapped in roofing material per detail 7/M0.02.  Currently, the sleepers
    are not wrapped.  See photo 81.	 	2/5/15	 	1	 	 	 	 	 	As Is - deleted by waterproofing consultant
	 	 	 	 	 	 	 	 	 	 	 	 	 
	26	 	Some
    vibration isolation pads under condensing units are not secured.  Many are in danger of falling off the wood sleeper.
    Continued vibration will cause pads to be displaced.  All should be fastened in place.  See photo 83 and 87.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	27	 	A bathroom
    exhaust fan in unit 138 makes a rattling noise.  At least 1 other unit on the 1st floor has a similar problem.  All
    should be checked and adjusted / repaired as necessary.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	28	 	Fan coil
    units in common areas are situated on concrete bricks.  The mechanical drawings specify these to be placed on 1⁄4-inch
    neoprene pads.  See photo 106.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	29	 	Condensate,
    T&P discharge and overflow pipe in HVAC closets are routed into a hub drain. Detail 5/P0.02 specifies that an air gap
    it to be maintained between the end of any drain pipe and the rim of the hub drain. This air gap is not maintained; pipe is
    routed deep into the mouth of the hub drain which presents the risk of backflow.  See photo 5.	 	2/5/15	 	1	 	 	 	 	 	As Is - per plumbing inspector's direction
	 	 	 	 	 	 	 	 	 	 	 	 	 
	30	 	An electrical
    opening near the exterior door at the east elevation is not complete.  See photo 63.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	31	 	A ground
    wire was found in one location in the courtyard not properly secured or buried which presents a trip hazard.  See photo
    111.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	32	 	An piece
    of Romex cable penetrates the wall above the fire door near unit 105 and is not terminated.  The purpose of the wire
    is uncertain.  See photo 174.	 	2/5/15	 	1	 	 	 	 	 	AH to address
	 	 	 	 	 	 	 	 	 	 	 	 	 
	33	 	Cracks
    have appeared at joints in finished wood trim in many apartment units.  See photo 28. This is due to natural drying which
    will disappear and reappear with seasonal humidity.	 	2/5/15	 	1	 	 	 	 	 	As Is
	 	 	 	 	 	 	 	 	 	 	 	 	 
	34	 	Detail
    8/A4.10 shows a 1x8 'crown mold' at apartments and corridors.  We observed no such molding in any location.	 	2/5/15	 	1	 	 	 	 	 	As Is - per A.10.07 no crown specified


 


		1	Seller to install landing area in front
                                         of gated entrance along south end of the apartment building to correct running slope
                                         to 2% through the installation of a compliant area of rescue. Item 2 on page 8 of ADA
                                         report.



		2	Landing in sidewalk to the gated entrance
                                         along south end of apartment building to be revised to 2% slope through the installation
                                         of a compliant area of rescue. Item 4 on page 8 of ADA report.



		3	Seller to correct cross slope to 2% on
                                         the accessible parking space located adjacent to the van accessible parking space on
                                         leasing office level. Item 6 on page 9 of ADA report.



		4	All of the common area doors to the leasing
                                         office restroom, community room, common area restrooms, the fitness center, and the computer
                                         room have opening door pressures greater than 5 lbs. Seller to address. Item 7 on page
                                         10 of ADA report.



		5	Seller to mount towel dispenser in fitness
                                         room to 48”. Item 8 on page 10 of ADA report.



		6	In unit 131 which is a B-4 type unit,
                                         the fridge to counter top width is 33” where 40” is required. Also, the counter
                                         top to counter top width is 39” where 40” is required.



    The
island portion of the cabinets should be moved away from the cabinets which contain the range and fridge in order to provide the
required 40” width. Seller to address. Item 10 on page 10 of ADA report.


		7	The accessible apartments units did not
                                         have accessible peep holes. Seller to address. Item 12 on page 11 of ADA report.



		8	In unit 445, which is a B-2 unit, the
                                         fridge to counter top width is 57” where 60” is required. This to be addressed
                                         by Seller in all three B-2 units. Item 15 on page 11 of ADA report.



		9	OPEN. Pending on code review, Seller
                                         required to provide 2% (5 additional units) audio/visual alert systems. Item 13 on page
                                         11 of ADA report.