Name: John M. McManus

Title: Vice President- Environmental Service

Company: American Electric Power

Sign Date: 6/30/2010

Name: Scott W. Banach

Title: Director, Project Engineering

Company: Platt Environmental Services, Inc.

Sign Date: 6/25/2010

Permitted Facility Representative / Date Testing Company Representative / Date

General James M. Gavin Unit 1- 8102

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, January 18, 2011 Page 1 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Facility Information:

General James M. Gavin Unit 1- 8102

7397 N. St. Rte. 7

Cheshire OH 45620

Contact: Paul Jackson

Phone: 614-716-3278

Fax: 614-716-1252

Email: pmjackson@aep.com

Testing Company:

Platt Environmental Services, Inc.

1520 Kensington Road

Suite 204

Oak Brook IL 60523

Contact: Scott Banach

Phone: 630-521-9400

Fax: 630-521-9494

Email: sbanach@plattenv.com

Air Permit Number:

06-27-01-0056

Permitted Source ID/Name:

0627010056 General James M. Gavin Unit 1

Permitted Maximum Process Rate:

11936 mmBTU/hr

Max. Normal Operation Process Rate:

11936 mmBTU/hr

Target Process Test Rate

11936 mmBTU/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Babcock and Wilcox model UP-102 pulverized coal-fired, dry-bottom boiler having a nominal capacity of 11,936 

mmBTU/hr, and controlled with a SCR, ESP and wet FGD.

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack 504 0 0 0 252 1008 4 6

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Hydrogen Fluoride Method 26A 3 0

Stack Hydrogen Chloride Method 26A 3 0

Stack O2 Method 3A O2 0

Stack Co2 Method 3A CO2 3 0

Tuesday, January 18, 2011 Page 2 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Tuesday, January 18, 2011 Page 3 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Sampling / Stack Data Results Summary

Location Stack - Method 26A

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 3/10/2010 3/10/2010 3/10/2010

Run Start Time 9:51:00 AM 12:12:00 

PM

2:05:00 PM

Run Finish Time 11:16:00 AM 1:32:00 PM 3:24:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 47.978 51.061 48.904 49.314

Moisture Content of Stack Gas, % 16.82 16.01 15.86 16.230

Moisture Saturation at Stack Gas Temperature, % 13.48 13.48 13.14 13.367

Carbon Dioxide, % 12.3 12.3 12.4 12.333

Oxygen, % 6.7 6.7 6.5 6.633

Average Stack Gas Temperature, °F 124.25 124.25 123.33 123.943

Dry Volumetric Flow Rate, dry scfm 3,650,383.7 3,644,149.1 3,578,354.0 3,624,295.60

0

Actual Wet Volumetric Flue Gas Flow Rate, acfm 4,867,057.7 4,858,745.1 4,744,861.8 4,823,554.86

7

Percent Isokinetic of Sampling Rate, % 100.8 107.4 104.8 104.333

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack - Method 3A CO2

Average

Run Number M26A-2 M26A-3 M26A1

Test Date 3/10/2010 3/10/2010 3/10/2010

Run Start Time 12:12:00 PM 2:05:00 PM 9:51:00 AM

Run Finish Time 1:32:00 PM 3:24:00 PM 11:16:00 AM

Carbon Dioxide, % 12.3 12.4 12.3 12.333

Oxygen, % 6.7 6.5 6.7 6.633

Dry Volumetric Flow Rate, dry scfm 3672931 3606012 3687636 3,655,526.33

3

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.5 13.2 13.5 13.400

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, January 18, 2011 Page 4 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Location Stack - Method 3A O2

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 3/10/2010 3/10/2010 3/10/2010

Run Start Time 9:51:00 AM 12:12:00 

PM

2:05:00 PM

Run Finish Time 11:16:00 AM 1:32:00 PM 3:24:00 PM

Carbon Dioxide, % 12.3 12.3 12.4 12.333

Oxygen, % 6.7 6.7 6.5 6.633

Dry Volumetric Flow Rate, dry scfm 3687636 3672931 3606012 3,655,526.33

3

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.5 13.5 13.2 13.400

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, January 18, 2011 Page 5 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Emissions Summary

Process Run Data

Location: Stack - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 18 18 18 18.000

lb/mmBtuO2 1.19E-02 1.12E-02 1.15E-02 0.012

Compound: Hydrogen Fluoride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 120 120 120 120.000

lb/mmBtuO2 7.94E-02 7.46E-02 7.68E-02 0.077

Tuesday, January 18, 2011 Page 6 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 1103 1000 tons/ hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1100

Tuesday, January 18, 2011 Page 7 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

1 Gross Load 1411 MW The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1400

Tuesday, January 18, 2011 Page 8 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

1 Total Excess Air 20.7 % The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

20

Tuesday, January 18, 2011 Page 9 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

1 NH3 flow 850 gal/hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

0

Tuesday, January 18, 2011 Page 10 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

1 Sorbent Injection Rate 1.5 Tons/hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1.5

Tuesday, January 18, 2011 Page 11 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

1 Main Steam Temperature 1000 F The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1000

Tuesday, January 18, 2011 Page 12 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

1 Main Steam Pressure 2584 psig The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

2600

Tuesday, January 18, 2011 Page 13 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 Bituminous Coal Burned 1108 1000 tons/ hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1100

Tuesday, January 18, 2011 Page 14 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 Gross Load 1411 MW The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1400

Tuesday, January 18, 2011 Page 15 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 Total Excess Air 20.54 % The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

20

Tuesday, January 18, 2011 Page 16 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 NH3 flow 850 gal/hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

0

Tuesday, January 18, 2011 Page 17 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 Sorbent Injection Rate 1.21 Tons/hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1.5

Tuesday, January 18, 2011 Page 18 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 Main Steam Temperature 1001 F The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1000

Tuesday, January 18, 2011 Page 19 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

2 Main Steam Pressure 2604 psig The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

2600

Tuesday, January 18, 2011 Page 20 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 Bituminous Coal Burned 1111 1000 tons/ hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1100

Tuesday, January 18, 2011 Page 21 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 Gross Load 1414 MW The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1400

Tuesday, January 18, 2011 Page 22 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 Total Excess Air 20.3 % The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

20

Tuesday, January 18, 2011 Page 23 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 NH3 flow 850 gal/hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

0

Tuesday, January 18, 2011 Page 24 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 Sorbent Injection Rate 1.36 Tons/hr The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1.5

Tuesday, January 18, 2011 Page 25 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 Main Steam Temperature 1000 F The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

1000

Tuesday, January 18, 2011 Page 26 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

3 Main Steam Pressure 2640 psig The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

2600

Tuesday, January 18, 2011 Page 27 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

APCD Run Data

Process Lab Run Data

1 0 The ERT requires 

that the process 

data collected 

during the stack 

test period be 

accompanied by a 

target value. For 

the AEP tests, we 

want to clarify that 

the target value 

provided does not 

represent any limit 

or maximum 

design set point for 

operation of the 

steam generators 

and associated 

control 

equipment. In 

some cases, the 

value is a permit or 

regulatory limit, 

such as the case of 

opacity. Operation 

outside of the 

target value does 

not represent 

abnormal 

operation.

0

Run Name Value UOM Comments

Target

Value

1 CATALYTIC REDUCTION 850 nh3 flow 850

2 CATALYTIC REDUCTION 850 nh3 flow 850

3 CATALYTIC REDUCTION 850 nh3 flow 850

1 WET SCRUBBER - HIGH EFFICIENCY Sorbent Injection Rate (tph) 1.5 1.5

2 WET SCRUBBER - HIGH EFFICIENCY 1.21 Sorbent Injection Rate (tph)1.5

3 WET SCRUBBER - HIGH EFFICIENCY 1.36 Sorbent Injection Rate (tph)1.5

1 ELECTROSTATIC PRECIPITATOR - HIGH 

EFFICIENCY

7 opacity (%) 10

2 ELECTROSTATIC PRECIPITATOR - HIGH 

EFFICIENCY

7.8 opacity (%) 10

3 ELECTROSTATIC PRECIPITATOR - HIGH 

EFFICIENCY

6.39 opacity (%) 10

Tuesday, January 18, 2011 Page 28 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Tuesday, January 18, 2011 Page 29 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Sampling / Stack Data Results Detail

Location Stack - Method 26A

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 3/10/2010 3/10/2010 3/10/2010

Run Start Time 9:51:00 AM 12:12:00 PM 2:05:00 PM

Run Finish Time 11:16:00 AM 1:32:00 PM 3:24:00 PM

Net Traversing Points 16 16 16

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.235 0.235 0.235 0.235

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1 1 1 1.000

Barometric Pressure, inches of Mercury 28.66 28.66 28.66 28.660

Average Orifice Meter Differential, inches H2O 1.89 1.88 1.82 1.863

Dry Gas Meter Volume Sampled, cubic feet 48.508 51.643 50.204 50.118

Average Dry Gas Meter Temperature, °F 53.83 54.00 61.63 56.487

Dry Gas Meter Volume Sampled, dscf 47.978 51.061 48.904 49.314

Total Moisture Liquid collected, g 206 206.8 195.8 202.867

Volume of Water Vapor, standard cubic feet 9.70 9.73 9.22 9.550

Moisture Content of Stack Gas, % 16.82 16.01 15.86 16.230

Moisture Saturation at Stack Gas Temperature, % 13.48 13.48 13.14 13.367

Dry Mole Fraction 0.8652 0.8652 0.8686 0.866

Carbon Dioxide, % 12.3 12.3 12.4 12.333

Oxygen, % 6.7 6.7 6.5 6.633

Carbon Monoxide & Nitrogen, % 81 81 81.1 81.033

Fuel Factor 1.15 1.15 1.16

Dry Molecular Weight, lb/lb-Mole 30.24 30.24 30.24 30.240

Wet Molecular weight, lb/lb-Mole 29.19 29.05 29.12 29.120

Flue Gas Static Pressure, inches of H2O 0.5 0.5 0.5 0.500

Absolute Flue Gas Pressure, inches of Mercury 28.70 28.70 28.70 28.700

Average Stack Gas Temperature, °F 124.25 124.25 123.33 123.943

Average Velocity Head, inches of H2O 0.9531128784

35802

0.945526822

507808

0.905057562

65526

0.935

Average Stack Gas Velocity, feet/second 58.55 58.45 57.08 58.027

Stack Cross-Sectional Area, square feet 1,385.442 1,385.442 1,385.442 1,385.442

Dry Volumetric Flow Rate, dry scfm 3,650,383.7 3,644,149.1 3,578,354.0 3,624,295.6

00

Actual Wet Volumetric Flue Gas Flow Rate, acfm 4,867,057.7 4,858,745.1 4,744,861.8 4,823,554.8

67

Percent Isokinetic of Sampling Rate, % 100.8 107.4 104.8 104.333

Percent Excess Air, % 45.6 45.6 43.6 44.933

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 504 504 504

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, January 18, 2011 Page 30 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Location Stack - Method 3A CO2

Average

Run Number M26A-2 M26A-3 M26A1

Test Date 3/10/2010 3/10/2010 3/10/2010

Run Start Time 12:12:00 PM 2:05:00 PM 9:51:00 AM

Run Finish Time 1:32:00 PM 3:24:00 PM 11:16:00 AM

Carbon Dioxide, % 12.3 12.4 12.3 12.333

Oxygen, % 6.7 6.5 6.7 6.633

Fuel Factor 1.15 1.16 1.15

Dry Volumetric Flow Rate, dry scfm 3672931 3606012 3687636 3,655,526.3

33

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.5 13.2 13.5 13.400

Analyzer Make Servomex Servomex Servomex

Analyzer Model 01440D1 01440D1 01440D1 14,400.000

Analyzer Serial Number 3951 3951 3951 3,951.000

Operating Range 25 25 25 25.000

Operating Units % % %

No. Readings/Avg. 80 79 70 76.333

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID CC203369-

co2

CC203369-

co2

CC203369-

co2

Calibration Pre Zero Cylinder Instrument Response 0 0.02 -0.02 0.000

Calibration Pre Zero Cylinder Bias 0.08 0.2 0 0.093

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC20938-co2 CC20938-

co2

CC20938-co2

Calibration Pre High Cylinder Instrument Response 9.95 9.95 9.95 9.950

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC203369-

co2

CC203369-

co2

CC203369-

co2

Calibration Post Zero Cylinder Instrument Response 0.02 0.01 0 0.010

Calibration Post Zero Cylinder Bias 0.16 0.15 0.1 0.137

Calibration Post Zero Cylinder Drift 0.08 0.05 0.1 0.077

Calibration Post High Cylinder ID CC20938-co2 CC20938-

co2

CC20938-co2

Calibration Post High Cylinder Instrument Response 9.95 9.97 9.95 9.957

Calibration Post High Cylinder Bias 0 0.1 0 0.033

Calibration Post High Cylinder Drift 0 0.1 0 0.033

Cavg 12.3 12.4 12.3 12.333

Cavg Units %vd %vd %vd

Cgas 12.3036 12.3925 12.2989 12.332

Cgas Units %vd %vd %vd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, January 18, 2011 Page 31 of 31
General James M. Gavin Unit 1- 8102

6/30/2010

Location Stack - Method 3A O2

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 3/10/2010 3/10/2010 3/10/2010

Run Start Time 9:51:00 AM 12:12:00 PM 2:05:00 PM

Run Finish Time 11:16:00 AM 1:32:00 PM 3:24:00 PM

Carbon Dioxide, % 12.3 12.3 12.4 12.333

Oxygen, % 6.7 6.7 6.5 6.633

Fuel Factor 1.15 1.15 1.16

Dry Volumetric Flow Rate, dry scfm 3687636 3672931 3606012 3,655,526.3

33

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.5 13.5 13.2 13.400

Analyzer Make Servomex Servomex Servomex

Analyzer Model 01440D1 01440D1 01440D1 14,400.000

Analyzer Serial Number 3951 3951 3951 3,951.000

Operating Range 25 25 25 25.000

Operating Units % % %

No. Readings/Avg. 80 80 79 79.667

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID SA10353-o2 SA10353-o2 SA10353-o2

Calibration Pre Zero Cylinder Instrument Response 0.08 0.03 0.1 0.070

Calibration Pre Zero Cylinder Bias 0 -0.2 0.08 -0.040

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC20938-o2 CC20938-o2 CC20938-o2

Calibration Pre High Cylinder Instrument Response 11.96 11.98 12.01 11.983

Calibration Pre High Cylinder Bias 0 0.08 0.2 0.093

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID SA10353-o2 SA10353-o2 SA10353-o2

Calibration Post Zero Cylinder Instrument Response 0.03 0.1 0.11 0.080

Calibration Post Zero Cylinder Bias -0.2 0.08 0.12 0.000

Calibration Post Zero Cylinder Drift 0.2 0.28 0.04 0.173

Calibration Post High Cylinder ID CC20938-o2 CC20938-o2 CC20938-o2

Calibration Post High Cylinder Instrument Response 11.98 12.01 12.07 12.020

Calibration Post High Cylinder Bias 0.08 0.2 0.44 0.240

Calibration Post High Cylinder Drift 0.08 0.12 0.24 0.147

Cavg 12.3 6.7 6.5 8.500

Cavg Units %vd %vd %vd

Cgas 12.3118 6.6628 6.4191 8.465

Cgas Units %vd %vd %vd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, January 18, 2011 Page 32 of 31