Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 1

 PERMIT

 Under the Environmental Conservation Law (ECL)

 IDENTIFICATION INFORMATION

Permit Type: Air Title V Facility

Permit ID: 2-6304-00024/00035

 Mod 0 Effective Date: 12/06/2006 Expiration Date: 12/05/2011

 Mod 1 Effective Date: 01/13/2009 Expiration Date: 12/05/2011

 Mod 2 Effective Date: Expiration Date: 

Permit Issued To:TC RAVENSWOOD LLC

 110 TURNPIKE RD STE 203

 WESTBOROUGH, MA 01581

Contact: KEN YAGER

 RAVENSWOOD GENERATING STATION

 38-54 VERNON BLVD

 LONG ISLAND CITY, NY 11101

 (718) 706-2702

Facility: RAVENSWOOD GENERATING STATION

 38-54 VERNON BLVD

 QUEENS, NY 11101

Contact: KEN YAGER

 RAVENSWOOD GENERATING STATION

 38-54 VERNON BLVD

 LONG ISLAND CITY, NY 11101

 (718) 706-2702

Description:

This facility consists of three (3) steam boiler turbine/generator sets and seventeen (17) simple

cycle combustion turbines with a combined nominal rating of 2,288 mw and three (3) emergency

generators. Natural gas is the primary fuel for all units, with low-sulfur #6 residual oil and/or

distillate fuel used when gas is unavailable.
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 2

By acceptance of this permit, the permittee agrees that the permit is contingent upon strict

compliance with the ECL, all applicable regulations, the General Conditions specified and any

Special Conditions included as part of this permit.

Permit Administrator: JOHN F CRYAN

 NYSDEC

 47-40 21ST ST

 LONG ISLAND CITY, NY 11101-5407

Authorized Signature: _________________________________ Date: ___ / ___ / _____
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 3

 Notification of Other State Permittee Obligations

Item A: Permittee Accepts Legal Responsibility and Agrees to Indemnification

 The permittee expressly agrees to indemnify and hold harmless the Department of

 Environmental Conservation of the State of New York, its representatives,

 employees and agents ("DEC") for all claims, suits, actions, and damages, to the

 extent attributable to the permittee's acts or omissions in connection with the

 compliance permittee's undertaking of activities in connection with, or operation

 and maintenance of, the facility or facilities authorized by the permit whether in

 compliance or not in any compliance with the terms and conditions of the permit.

 This indemnification does not extend to any claims, suits, actions, or damages to

 the extent attributable to DEC's own negligent or intentional acts or omissions, or

 to any claims, suits, or actions naming the DEC and arising under article 78 of the 

 New York Civil Practice Laws and Rules or any citizen suit or civil rights

 provision under federal or state laws.

Item B: Permittee's Contractors to Comply with Permit

 The permittee is responsible for informing its independent contractors, employees,

 agents and assigns of their responsibility to comply with this permit, including all

 special conditions while acting as the permittee's agent with respect to the

 permitted activities, and such persons shall be subject to the same sanctions for

 violations of the Environmental Conservation Law as those prescribed for the

 permittee.

Item C: Permittee Responsible for Obtaining Other Required Permits

 The permittee is responsible for obtaining any other permits, approvals, lands, 

 easements and rights-of-way that may be required to carry out the activities that

 are authorized by this permit.

Item D: No Right to Trespass or Interfere with Riparian Rights

 This permit does not convey to the permittee any right to trespass upon the lands

 or interfere with the riparian rights of others in order to perform the permitted 

 work nor does it authorize the impairment of any rights, title, or interest in real or

 personal property held or vested in a person not a party to the permit.
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 4

 LIST OF CONDITIONS

 

 DEC GENERAL CONDITIONS

 General Provisions

 Facility Inspection by the Department

 Facility Inspection by the Department

 Relationship of this Permit to Other Department Orders and

 Determinations

 Relationship of this Permit to Other Department Orders and

 Determinations

 Applications for permit renewals, modifications and transfers

 Applications for permit renewals, modifications and transfers

 Applications for Permit Renewals and Modifications

 Permit modifications, suspensions or revocations by the Department

 Permit modifications, suspensions or revocations by the Department

 Permit Modifications, Suspensions and Revocations by the Department

 Facility Level

 Submission of Applications for Permit Modification or

 Renewal-REGION 2 HEADQUARTERS

 Submission of application for permit modification or renewal -

 REGION 2 HEADQUARTERS
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 5

 DEC GENERAL CONDITIONS

 **** General Provisions  

 For the purpose of your Title V permit, the following section contains

 state-only enforceable terms and conditions.

 GENERAL CONDITIONS - Apply to ALL Authorized Permits.

Condition 1: Facility Inspection by the Department

 Applicable State Requirement: ECL 19-0305

Item 1.1:

The permitted site or facility, including relevant records, is subject to inspection at reasonable

hours and intervals by an authorized representative of the Department of Environmental

Conservation (the Department) to determine whether the permittee is complying with this permit

and the ECL. Such representative may order the work suspended pursuant to ECL 71-0301 and

SAPA 401(3).

Item 1.2:

The permittee shall provide a person to accompany the Department's representative during an

inspection to the permit area when requested by the Department.

Item 1.3:

A copy of this permit, including all referenced maps, drawings and special conditions, must be

available for inspection by the Department at all times at the project site or facility. Failure to

produce a copy of the permit upon request by a Department representative is a violation of this

permit.

Condition 2-1: Facility Inspection by the Department

 Applicable State Requirement: ECL 19-0305

Item 2-1.1:

The permitted site or facility, including relevant records, is subject to inspection at reasonable

hours and intervals by an authorized representative of the Department of Environmental

Conservation (the Department) to determine whether the permittee is complying with this permit

and the ECL. Such representative may order the work suspended pursuant to ECL 71-0301 and

SAPA 401(3).

Item 2-1.2:

The permittee shall provide a person to accompany the Department's representative during an

inspection to the permit area when requested by the Department.

Item 2-1.3:

A copy of this permit, including all referenced maps, drawings and special conditions, must be

available for inspection by the Department at all times at the project site or facility. Failure to

produce a copy of the permit upon request by a Department representative is a violation of this

permit.

Condition 2: Relationship of this Permit to Other Department Orders and Determinations

 Applicable State Requirement: ECL 3-0301 (2) (m)

Item 2.1:

Unless expressly provided for by the Department, issuance of this permit does not modify,

supersede or rescind any order or determination previously issued by the Department or any of
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 6

the terms, conditions or requirements contained in such order or determination.

Condition 2-2: Relationship of this Permit to Other Department Orders and

Determinations

 Applicable State Requirement: ECL 3-0301 (2) (m)

Item 2-2.1:

Unless expressly provided for by the Department, issuance of this permit does not modify,

supersede or rescind any order or determination previously issued by the Department or any of

the terms, conditions or requirements contained in such order or determination.

Condition 2-3: Applications for permit renewals, modifications and transfers

 Applicable State Requirement: 6 NYCRR 621.11

Item 2-3.1:

The permittee must submit a separate written application to the Department for renewal,

modification or transfer of this permit. Such application must include any forms or supplemental

information the Department requires. Any renewal, modification or transfer granted by the

Department must be in writing.

Item 2-3.2:

The permittee must submit a renewal application at least 180 days before expiration of permits

for Title V Facility Permits, or at least 30 days before expiration of permits for State Facility

Permits. 

Item 2-3.3:

Permits are transferrable with the approval of the department unless specifically prohibited by

the statute, regulation or another permit condition. Applications for permit transfer should be

submitted prior to actual transfer of ownership.

Condition 4: Applications for permit renewals, modifications and transfers

 Applicable State Requirement: 6 NYCRR 621.11

Item 4.1:

The permittee must submit a separate written application to the Department for renewal,

modification or transfer of this permit. Such application must include any forms or supplemental

information the Department requires. Any renewal, modification or transfer granted by the

Department must be in writing.

Item 4.2:

The permittee must submit a renewal application at least 180 days before expiration of permits

for Title V Facility Permits, or at least 30 days before expiration of permits for State Facility

Permits. 

Item 4.3:

Permits are transferrable with the approval of the department unless specifically prohibited by

the statute, regulation or another permit condition. Applications for permit transfer should be

submitted prior to actual transfer of ownership.

Condition 3: Applications for Permit Renewals and Modifications

 Applicable State Requirement: 6 NYCRR 621.13

Item 3.1:
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 7

The permittee must submit a separate written application to the Department for renewal,

modification or transfer of this permit. Such application must include any forms or supplemental

information the Department requires. Any renewal, modification or transfer granted by the

Department must be in writing.

Item 3.2:

The permittee must submit a renewal application at least 180 days before expiration of permits

for Title V Facility Permits, or at least 30 days before expiration of permits for State Facility

Permits. 

Item 3.3:

Permits are transferrable with the approval of the department unless specifically prohibited by

the statute, regulation or another permit condition. Applications for permit transfer should be

submitted prior to actual transfer of ownership.

Condition 2-4: Permit modifications, suspensions or revocations by the

Department

 Applicable State Requirement: 6 NYCRR 621.13

Item 2-4.1:

The Department reserves the right to exercise all available authority to modify, suspend, or

revoke this permit in accordance with 6NYCRR Part 621. The grounds for modification,

suspension or revocation include:

a) materially false or inaccurate statements in the permit application or supporting papers;

b) failure by the permittee to comply with any terms or conditions of the permit;

c) exceeding the scope of the project as described in the permit application;

d) newly discovered material information or a material change in environmental conditions,

relevant technology or applicable law or regulations since the issuance of the existing permit;

e) noncompliance with previously issued permit conditions, orders of the commissioner, any

provisions of the Environmental Conservation Law or regulations of the Department related to

the permitted activity.

Condition 5: Permit modifications, suspensions or revocations by the Department

 Applicable State Requirement: 6 NYCRR 621.13

Item 5.1:

The Department reserves the right to modify, suspend, or revoke this permit in accordance with

6NYCRR Part 621. The grounds for modification, suspension or revocation include:

 a) materially false or inaccurate statements in the permit application or supporting

papers;

 b) failure by the permittee to comply with any terms or conditions of the permit;

 c) exceeding the scope of the project as described in the permit application;

 d) newly discovered material information or a material change in environmental

conditions, relevant technology or applicable law or regulations since the issuance of the

existing permit;

 e) noncompliance with previously issued permit conditions, orders of the

commissioner, any provisions of the Environmental Conservation Law or regulations of

the Department related to the permitted activity.

Condition 6: Permit Modifications, Suspensions and Revocations by the Department
 

Facility DEC ID: 2630400024

 DEC Permit Conditions

 Renewal 1/Mod 2/DRAFT Page 8

 Applicable State Requirement: 6 NYCRR 621.14

Item 6.1:

The Department reserves the right to modify, suspend, or revoke this permit in accordance with

6NYCRR Part 621. The grounds for modification, suspension or revocation include:

 a) materially false or inaccurate statements in the permit application or supporting

papers;

 b) failure by the permittee to comply with any terms or conditions of the permit;

 c) exceeding the scope of the project as described in the permit application;

 d) newly discovered material information or a material change in environmental

conditions, relevant technology or applicable law or regulations since the issuance of the

existing permit;

 e) noncompliance with previously issued permit conditions, orders of the

commissioner, any provisions of the Environmental Conservation Law or regulations of

the Department related to the permitted activity.

 ** ** Facility Level  

Condition 7: Submission of Applications for Permit Modification or Renewal-REGION 2 

 HEADQUARTERS

 Applicable State Requirement: 6 NYCRR 621.5 (a)

Item 7.1:

Submission of applications for permit modification or renewal are to be submitted to:

 NYSDEC Regional Permit Administrator 

 Region 2 Headquarters

 Division of Environmental Permits

 1 Hunters Point Plaza, 4740 21st Street

 Long Island City, NY 11101-5407 

 (718) 482-4997

Condition 2-5: Submission of application for permit modification or renewal -

REGION 2 

 HEADQUARTERS

 Applicable State Requirement: 6 NYCRR 621.6 (a)

Item 2-5.1:

Submission of applications for permit modification or renewal are to be submitted to:

 NYSDEC Regional Permit Administrator 

 Region 2 Headquarters

 Division of Environmental Permits

 1 Hunters Point Plaza, 4740 21st Street

 Long Island City, NY 11101-5407 

 (718) 482-4997 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 1 DRAFT

 Permit Under the Environmental Conservation Law (ECL)

 ARTICLE 19: AIR POLLUTION CONTROL - TITLE V PERMIT

 IDENTIFICATION INFORMATION

Permit Issued To:TC RAVENSWOOD LLC

 110 TURNPIKE RD STE 203

 WESTBOROUGH, MA 01581

Facility: RAVENSWOOD GENERATING STATION

 38-54 VERNON BLVD

 QUEENS, NY 11101

Authorized Activity By Standard Industrial Classification Code:

 4911 - ELECTRIC SERVICES

Permit Effective Date: Permit Expiration Date: 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 2 DRAFT

 LIST OF CONDITIONS

 

 FEDERALLY ENFORCEABLE CONDITIONS

 Facility Level

 2-1 6 NYCRR 201-6.5 (a) (7): Fees

 2-2 6 NYCRR 215.2: Open Fires - Prohibitions

 2-3 6 NYCRR 201-1.8: Prohibition of Reintroduction of Collected 

 Contaminants to the air

 2-4 6 NYCRR 202-1.1: Required Emissions Tests

 23 6 NYCRR Subpart 201-6: Emission Unit Definition

 2-5 6 NYCRR 211.1: Air pollution prohibited

 2-6 6 NYCRR 249.3 (a): Compliance Certification

 2-7 6 NYCRR 249.3 (a): Compliance Certification

 2-8 6 NYCRR 249.3 (a): Compliance Certification

 2-9 6 NYCRR 249.3 (d): Compliance Certification

 Emission Unit Level

 53 6 NYCRR Subpart 201-6: Process Definition By Emission Unit

 EU=U-00010

 2-10 6 NYCRR 249.3 (f): Compliance Certification

 EU=U-00020

 2-11 6 NYCRR 249.3 (f): Compliance Certification

 EU=U-00030

 2-12 6 NYCRR 249.3 (f): Compliance Certification

 STATE ONLY ENFORCEABLE CONDITIONS

 Facility Level

 85 ECL 19-0301: Contaminant List

 2-13 6 NYCRR 201-1.4: Unavoidable noncompliance and violations

 2-14 6 NYCRR 211.2: Visible Emissions Limited
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 3 DRAFT

 FEDERALLY ENFORCEABLE CONDITIONS

 ** ** Facility Level  

 NOTIFICATION OF GENERAL PERMITTEE OBLIGATIONS

 The items listed below are not subject to the annual compliance certification

 requirements under Title V. Permittees may also have other obligations

 under regulations of general applicability.

Item A: Emergency Defense - 6 NYCRR 201-1.5

 An emergency constitutes an affirmative defense to an 

 action brought for noncompliance with emissions 

 limitations or permit conditions for all facilities in New

 York State.

 (a) The affirmative defense of emergency shall be 

 demonstrated through properly signed, contemporaneous 

 operating logs, or other relevant evidence that:

 (1) An emergency occurred and that the facility owner 

 and/or

 operator can identify the cause(s) of the 

 emergency;

 (2) The equipment at the permitted facility causing the

 emergency was at the time being properly operated;

 (3) During the period of the emergency the facility owner

 and/or operator took all reasonable steps to minimize 

 levels of emissions that exceeded the emission standards, 

 or other requirements in the permit; and

 (4) The facility owner and/or operator notified the 

 Department

 within two working days after the event occurred. This 

 notice must contain a description of the emergency, any 

 steps taken to mitigate emissions, and corrective actions 

 taken.

 (b) In any enforcement proceeding, the facility owner 

 and/or operator seeking to establish the occurrence of an 

 emergency has the burden of proof.

 (c) This provision is in addition to any emergency or 

 upset provision contained in any applicable requirement.

Item B: Public Access to Recordkeeping for Title V Facilities - 6

 NYCRR 201-1.10 (b)

 The Department will make available to the public any 

 permit application, compliance plan, permit, and 

 monitoring and compliance certification report pursuant to

 Section 503(e) of the Act, except for information entitled

 to confidential treatment pursuant to 6 NYCRR Part 616 - 

 Public Access to records and Section 114(c) of the Act.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 4 DRAFT

Item C: Timely Application for the Renewal of Title V Permits - 6

 NYCRR 201-6.3 (a) (4)

 Owners and/or operators of facilities having an issued 

 Title V permit shall submit a complete application at 

 least 180 days, but not more than eighteen months, prior 

 to the date of permit expiration for permit renewal 

 purposes.

Item D: Certification by a Responsible Official - 6 NYCRR 201-6.3

 (d) (12)

 Any application, form, report or compliance certification

 required to be submitted pursuant to the federally 

 enforceable portions of this permit shall contain a 

 certification of truth, accuracy and completeness by a 

 responsible official. This certification shall state that 

 based on information and belief formed after reasonable 

 inquiry, the statements and information in the document 

 are true, accurate, and complete.

Item E: Requirement to Comply With All Conditions - 6 NYCRR 

 201-6.5 (a) (2)

 The permittee must comply with all conditions of the 

 Title V facility permit. Any permit non-compliance 

 constitutes a violation of the Act and is grounds for 

 enforcement action; for permit termination, revocation and

 reissuance, or modification; or for denial of a permit 

 renewal application.

Item F: Permit Revocation, Modification, Reopening, Reissuance or

 Termination, and Associated Information Submission 

 Requirements - 6 NYCRR 201-6.5 (a) (3)

 This permit may be modified, revoked, reopened and 

 reissued, or terminated for cause. The filing of a request

 by the permittee for a permit modification, revocation and

 reissuance, or termination, or of a notification of 

 planned changes or anticipated noncompliance does not stay

 any permit condition.

Item G: Cessation or Reduction of Permitted Activity Not a 

 Defense - 6 NYCRR 201-6.5 (a) (5)

 It shall not be a defense for a permittee in an 

 enforcement action to claim that a cessation or reduction 

 in the permitted activity would have been necessary in 

 order to maintain compliance with the conditions of this 

 permit.

Item H: Property Rights - 6 NYCRR 201-6.5 (a) (6)

 This permit does not convey any property rights of any 

 sort or any exclusive privilege.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 5 DRAFT

Item I: Severability - 6 NYCRR 201-6.5 (a) (9)

 If any provisions, parts or conditions of this permit are

 found to be invalid or are the subject of a challenge, the

 remainder of this permit shall continue to be valid.

Item J: Permit Shield - 6 NYCRR 201-6.5 (g)

 All permittees granted a Title V facility permit shall be

 covered under the protection of a permit shield, except as

 provided under 6 NYCRR Subpart 201-6. Compliance with the

 conditions of the permit shall be deemed compliance with 

 any applicable requirements as of the date of permit 

 issuance, provided that such applicable requirements are 

 included and are specifically identified in the permit, or

 the Department, in acting on the permit application or 

 revision, determines in writing that other requirements 

 specifically identified are not applicable to the major 

 stationary source, and the permit includes the 

 determination or a concise summary thereof. Nothing herein

 shall preclude the Department from revising or revoking 

 the permit pursuant to 6 NYCRR Part 621 or from exercising

 its summary abatement authority. Nothing in this permit 

 shall alter or affect the following:

 i. The ability of the Department to seek to bring suit

 on behalf of the State of New York, or the Administrator 

 to seek to bring suit on behalf of the United States, to 

 immediately restrain any person causing or contributing to

 pollution presenting an imminent and substantial 

 endangerment to public health, welfare or the environment 

 to stop the emission of air pollutants causing or 

 contributing to such pollution;

 ii. The liability of a permittee of the Title V 

 facility for any violation of applicable requirements 

 prior to or at the time of permit issuance;

 iii. The applicable requirements of Title IV of the 

 Act;

 iv. The ability of the Department or the Administrator

 to obtain information from the permittee concerning the 

 ability to enter, inspect and monitor the facility.

Item K: Reopening for Cause - 6 NYCRR 201-6.5 (i)

 This Title V permit shall be reopened and revised under 

 any of the following circumstances:

 i. If additional applicable requirements under the Act

 become applicable where this permit's remaining term is 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 6 DRAFT

 three or more years, a reopening shall be completed not 

 later than 18 months after promulgation of the applicable 

 requirement. No such reopening is required if the 

 effective date of the requirement is later than the date 

 on which this permit is due to expire, unless the original

 permit or any of its terms and conditions has been 

 extended by the Department pursuant to the provisions of 

 Part 201-6.7 and Part 621.

 ii. The Department or the Administrator determines 

 that the permit contains a material mistake or that 

 inaccurate statements were made in establishing the 

 emissions standards or other terms or conditions of the 

 permit.

 iii. The Department or the Administrator determines 

 that the Title V permit must be revised or reopened to 

 assure compliance with applicable requirements.

 iv. If the permitted facility is an "affected source" 

 subject to the requirements of Title IV of the Act, and 

 additional requirements (including excess emissions 

 requirements) become applicable. Upon approval by the 

 Administrator, excess emissions offset plans shall be 

 deemed to be incorporated into the permit.

 Proceedings to reopen and issue Title V facility permits 

 shall follow the same procedures as apply to initial 

 permit issuance but shall affect only those parts of the 

 permit for which cause to reopen exists.

 Reopenings shall not be initiated before a notice of such

 intent is provided to the facility by the Department at 

 least thirty days in advance of the date that the permit 

 is to be reopened, except that the Department may provide

 a shorter time period in the case of an emergency.

Item L: Permit Exclusion - ECL 19-0305

 The issuance of this permit by the Department and the 

 receipt thereof by the Applicant does not and shall not be

 construed as barring, diminishing, adjudicating or in any 

 way affecting any legal, administrative or equitable 

 rights or claims, actions, suits, causes of action or 

 demands whatsoever that the Department may have against 

 the Applicant for violations based on facts and 

 circumstances alleged to have occurred or existed prior to

 the effective date of this permit, including, but not 

 limited to, any enforcement action authorized pursuant to 

 the provisions of applicable federal law, the 

 Environmental Conservation Law of the State of New York 

 (ECL) and Chapter III of the Official Compilation of the 

 Codes, Rules and Regulations of the State of New York 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 7 DRAFT

 (NYCRR). The issuance of this permit also shall not in any

 way affect pending or future enforcement actions under the

 Clean Air Act brought by the United States or any person.

Item M: Federally Enforceable Requirements - 40 CFR 70.6 (b)

 All terms and conditions in this permit required by the 

 Act or any applicable requirement, including any 

 provisions designed to limit a facility's potential to 

 emit, are enforceable by the Administrator and citizens 

 under the Act. The Department has, in this permit, 

 specifically designated any terms and conditions that are 

 not required under the Act or under any of its applicable 

 requirements as being enforceable under only state 

 regulations.

 MANDATORY FEDERALLY ENFORCEABLE PERMIT CONDITIONS 

 SUBJECT TO ANNUAL CERTIFICATIONS AT ALL TIMES

 The following federally enforceable permit conditions are mandatory for all

 Title V permits and are subject to annual compliance certification 

 requirements at all times.

Condition 2-1: Fees

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (7)

Item 2-1.1:

The owner and/or operator of a stationary source shall pay fees to the Department consistent

with the fee schedule authorized by ECL 72-0303.

Condition 2-2: Open Fires - Prohibitions

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 215.2

Item 2-2.1: 

Except as allowed by Title 6 NYCRR Section 215.3, no person shall burn, cause, suffer, allow

or permit the burning of any materials in an open fire.

Item 2-2.2

Per Section 215.3, burning in an open fire, provided it is not contrary to other law or regulation,

will be allowed as follows:

(a) On-site burning in any town with a total population less than 20,000 of downed limbs and

branches (including branches with attached leaves or needles) less than six inches in diameter

and eight feet in length between May 15th and the following March 15th. For the purposes of

this subdivision, the total population of a town shall include the population of any village or

portion thereof located within the town. However, this subdivision shall not be construed to

allow burning within any village.

(b) Barbecue grills, maple sugar arches and similar outdoor cooking devices when actually used
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 8 DRAFT

for cooking or processing food.

(c) Small fires used for cooking and camp fires provided that only charcoal or untreated wood is

used as fuel and the fire is not left unattended until extinguished.

(d) On-site burning of agricultural wastes as part of a valid agricultural operation on contiguous

agricultural lands larger than five acres actively devoted to agricultural or horticultural use,

provided such waste is actually grown or generated on those lands and such waste is capable of

being fully burned within a 24-hour period.

(e) The use of liquid petroleum fueled smudge pots to prevent frost damage to crops.

(f) Ceremonial or celebratory bonfires where not otherwise prohibited by law, provided that only

untreated wood or other agricultural products are used as fuel and the fire is not left unattended

until extinguished.

(g) Small fires that are used to dispose of a flag or religious item, and small fires or other smoke

producing process where not otherwise prohibited by law that are used in connection with a

religious ceremony.

(h) Burning on an emergency basis of explosive or other dangerous or contraband materials by

police or other public safety organization.

(i) Prescribed burns performed according to Part 194 of this Title.

(j) Fire training, including firefighting, fire rescue, and fire/arson investigation training,

performed under applicable rules and guidelines of the New York State Department of State's

Office of Fire Prevention and Control. For fire training performed on acquired structures, the

structures must be emptied and stripped of any material that is toxic, hazardous or likely to emit

toxic smoke (such as asbestos, asphalt shingles and vinyl siding or other vinyl products) prior to

burning and must be at least 300 feet from other occupied structures. No more than one structure

per lot or within a 300 foot radius (whichever is bigger) may be burned in a training exercise.

(k) Individual open fires as approved by the Director of the Division of Air Resources as may be

required in response to an outbreak of a plant or animal disease upon request by the

commissioner of the Department of Agriculture and Markets, or for the destruction of invasive

plant and insect species.

(l) Individual open fires that are otherwise authorized under the environmental conservation law,

or by rule or regulation of the Department.

 MANDATORY FEDERALLY ENFORCEABLE PERMIT CONDITIONS 

 SUBJECT TO ANNUAL CERTIFICATIONS ONLY IF APPLICABLE

 The following federally enforceable permit conditions are mandatory for all 

 Title V permits and are subject to annual compliance certification 

 requirements only if effectuated during the reporting period.

 [NOTE: The corresponding annual compliance certification for 

 those conditions not effectuated during the reporting period shall 

 be specified as "not applicable".]

Condition 2-3: Prohibition of Reintroduction of Collected Contaminants to

 the air

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 201-1.8

Item 2-3.1:

No person shall unnecessarily remove, handle or cause to be handled, collected air contaminants

from an air cleaning device for recycling, salvage or disposal in a manner that would reintroduce
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 9 DRAFT

them to the outdoor atmosphere.

Condition 2-4: Required Emissions Tests

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 202-1.1

Item 2-4.1:

For the purpose of ascertaining compliance or non-compliance with any air pollution control

code, rule or regulation, the commissioner may require the person who owns such air

contamination source to submit an acceptable report of measured emissions within a stated time.

 The following conditions are subject to annual compliance certification 

 requirements for Title V permits only.

Condition 23: Emission Unit Definition

 Effective between the dates of 12/06/2006 and Permit Expiration Date

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 23.1(From Mod 2):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00010 

 Emission Unit Description: 

 THIS UNIT CONSISTS OF DUAL, TANGENTIALLY 

 FIRED FURNACES COMPRISING A SINGLE BOILER. 

 STEAM FROM THIS BOILER OPERATES A TANDEM 

 TURBINE GENERATOR SET NOMINALLY RATED AT 

 390 MW. THE FURNACES OPERATE ON NATUAL GAS

 OR LOW SULFUR #6 RESIDUAL OIL. ON 

 OCCASION, SMALL AMOUNTS OF WASTE FUEL A MAY

 BE FIRED IN CONJUNCTION WITH THE PRIMARY 

 FUEL. ON AN INFREQUENT BASIS, 

 NON-HAZARDOUS BOILER CLEANING SOLUTION MAY 

 BE EVAPORATED IN THIS UNIT IN CONJUNCTION 

 WITH THE PRIMARY FUEL. 

 CLOSE COUPLED OVER-FIRED AIR (CCOFA) 

 COMPARTMENTS HAVE BEEN ADDED TO THE UPPER 

 AND LOWER WINDBOX SECTIONS OF THIS EMISSION

 UNIT. CCOFA IS A PROVEN NOx REDUCTION 

 TECHNOLOGY AND WAS INSTALLED AS PART OF 

 KEYSPAN'S PLAN TO MEET PHASE III OF THE NOx

 BUDGET REQUIREMENTS. INSTALLATION OCCURRED

 DURING THE FALL 2000 SCHEDULED OUTAGE.

 Building(s): GEN STA
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 10 DRAFT

Item 23.2(From Mod 2):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00020 

 Emission Unit Description: 

 THIS UNIT CONSISTS OF DUAL, TANGENTIALLY 

 FIRED FURNACES COMPRISING A SINGLE BOILER. 

 STEAM FROM THIS BOILER OPERATES A TANDEM 

 TURBINE GENERATOR SET NOMINALLY RATED AT 

 390 MW. THIS BOILER IS EQUIPPED WITH A 

 CLOSE-COUPLED-OVERFIRED-AIR (CCOFA) SYSTEM 

 TO REDUCE THE FORMATION OF NITROGEN OXIDES.

 THE FURNACES OPERATE ON NATURAL GAS OR LOW

 SULFUR #6 RESIDUAL OIL. ON OCCASION, SMALL

 AMOUNTS OF WASTE FUEL A MAY BE FIRED IN 

 CONJUNCTION WITH THE PRIMARY FUEL. ON AN 

 INFREQUENT BASIS, NON-HAZARDOUS BOILER 

 CLEANING SOLUTIONS MAY BE EVAPORATED IN 

 THIS UNIT IN CONJUNCTION WITH PRIMARY 

 FUEL.

 Building(s): GEN STA

Item 23.3(From Mod 2):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00030 

 Emission Unit Description: 

 THIS UNIT CONSISTS OF DUAL BOILERS, EACH 

 HEATED BY DUAL, TANGENTIALLY FIRED 

 FURNACES. STEAM FROM THESE BOILERS 

 OPERATES A TANDEM TURBINE GENERATOR SET 

 NOMINALLY RATED AT 972 MW. KEYSPAN WILL BE

 INSTALLING A CLOSE-COUPLED-OVERFIRED-AIR 

 (CCOFA) SYSTEM BY LATE 2001 TO FURTHER 

 REDUCE THE FORMATION OF NITROGEN OXIDES. 

 THE FURNACES OPERATE ON NATURAL GAS OR LOW 

 SULFUR #6 RESIDUAL OIL. ON OCCASION, SMALL

 AMOUNTS OF WASTE FUEL A MAY BE FIRED IN 

 CONJUNCTION WITH THE PRIMARY FUEL. ON AN 

 INFREQUENT BASIS, NON-HAZARDOUS BOILER 

 CLEANING SOLUTION MAY BE EVAPORATED IN THIS

 UNIT IN CONJUNCTION WITH THE PRIMARY FUEL.

 Building(s): GEN STA

Item 23.4(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT001 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. THIS UNIT IS A 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 11 DRAFT

 "BLACK-START" COMBUSTION TURBINE DESIGNED 

 TO PROVIDE SUFFICIENT POWER TO BRING THE 

 ENTIRE POWER STATION BACK ON-LINE FOLLOWING

 A CATASTROPHIC SYSTEM COLLAPSE. A DIESEL 

 ENGINE, EMISSION POINT GT0S1, EMISSION UNIT

 U-CT0S1 IS UTILIZED TO START THIS 

 COMBUSTION TURBINE.

 Building(s): GT1

Item 23.5(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT004 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. A DIESEL ENGINE, 

 EMISSION POINT GT0S4, EMISSION UNIT U-CT0S4

 IS UTILIZED TO START THIS COMBUSTION 

 TURBINE.

 Building(s): CT4

Item 23.6(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT005 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. A DIESEL ENGINE, 

 EMISSION POINT GT0S5, EMISSION UNIT U-CT0S5

 IS UTILIZED TO START THIS COMBUSTION 

 TURBINE.

 Building(s): CT5

Item 23.7(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT006 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. A DIESEL ENGINE, 

 EMISSION POINT GT0S6, EMISSION UNIT U-CT0S6

 IS UTILIZED TO START THIS COMBUSTION 

 TURBINE.

 Building(s): CT6
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 12 DRAFT

Item 23.8(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT007 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. A DIESEL ENGINE, 

 EMISSION POINT GT0S7, EMISSION UNIT U-CT0S7

 IS UTILIZED TO START THIS COMBUSTION 

 TURBINE.

 Building(s): CT7

Item 23.9(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT008 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM.

 Building(s): CT8

Item 23.10(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT009 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM.

 Building(s): CT9

Item 23.11(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT010 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM.

 Building(s): CT10

Item 23.12(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT011 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 13 DRAFT

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM.

 Building(s): CT11

Item 23.13(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT0S1 

 Emission Unit Description: 

 THIS UNIT IS A 430 HP DIESEL ENGINE USED 

 TO START THE "BLACK-START" COMBUSTION 

 TURBINE, DESIGNATED EMISSION UNIT U-CT001. 

 THIS UNIT ONLY OPERATES DURING START-UP OF 

 THE COMBUSTION TURBINE, GENERALLY LESS THAN

 15 MINUTES PER EVENT.

 Building(s): CT1

Item 23.14(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT0S4 

 Emission Unit Description: 

 THIS UNIT IS A 430 HP DIESEL ENGINE USED 

 TO START THE "BLACK-START" COMBUSTION 

 TURBINE, DESIGNATED EMISSION UNIT U-CT004. 

 THIS UNIT ONLY OPERATES DURING START-UP OF 

 THE COMBUSTION TURBINE, GENERALLY LESS THAN

 15 MINUTES PER EVENT.

 Building(s): CT4

Item 23.15(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT0S5 

 Emission Unit Description: 

 THIS UNIT IS A 430 HP DIESEL ENGINE USED 

 TO START THE "BLACK-START" COMBUSTION 

 TURBINE, DESIGNATED EMISSION UNIT U-CT005. 

 THIS UNIT ONLY OPERATES DURING START-UP OF 

 THE COMBUSTION TURBINE, GENERALLY LESS THAN

 15 MINUTES PER EVENT.

 Building(s): CT5

Item 23.16(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT0S6 

 Emission Unit Description: 

 THIS UNIT IS A 430 HP DIESEL ENGINE USED 

 TO START THE "BLACK-START" COMBUSTION 

 TURBINE, DESIGNATED EMISSION UNIT U-CT006. 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 14 DRAFT

 THIS UNIT ONLY OPERATES DURING START-UP OF 

 THE COMBUSTION TURBINE, GENERALLY LESS THAN

 15 MINUTES PER EVENT.

 Building(s): CT6

Item 23.17(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT0S7 

 Emission Unit Description: 

 THIS UNIT IS A 430 HP DIESEL ENGINE USED 

 TO START THE "BLACK-START" COMBUSTION 

 TURBINE, DESIGNATED EMISSION UNIT U-CT007. 

 THIS UNIT ONLY OPERATES DURING START-UP OF 

 THE COMBUSTION TURBINE, GENERALLY LESS THAN

 15 MINUTES PER EVENT.

 Building(s): CT7

Item 23.18(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT201 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT21

Item 23.19(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT202 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 15 DRAFT

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT22

Item 23.20(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT203 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT23

Item 23.21(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT204 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 16 DRAFT

 Building(s): CT24

Item 23.22(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT301 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT31

Item 23.23(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT302 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT32

Item 23.24(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT303 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 17 DRAFT

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT33

Item 23.25(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-CT304 

 Emission Unit Description: 

 THIS UNIT IS A COMBUSTION TURBINE USED TO 

 SUPPLY PEAK GENERATION CAPACITY, AS 

 REQUIRED TO SUPPORT THE NYC ELECTRIC 

 DISTRIBUTION SYSTEM. TWO TURBINE ENGINES 

 DRIVE A SINGLE GENERATOR AND EXHAUST 

 THROUGH A COMMON STACK. Inlet water spray

 may be utilized for NOx reduction. Based 

 on stack test results for carbon monoxide, 

 operation of this unit shall be restricted 

 such that the 365 day rolling summation of 

 CO mass emissions shall not exceed that 

 which would have been released during 4,171

 (3,672 hr in ozone season plus 499 

 non-ozone season operation) hours of 

 operation without inlet spray.

 Building(s): CT34

Condition 2-5: Air pollution prohibited

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 211.1

Item 2-5.1:

No person shall cause or allow emissions of air contaminants to the outdoor atmosphere of such

quantity, characteristic or duration which are injurious to human, plant or animal life or to

property, or which unreasonably interfere with the comfortable enjoyment of life or property.

Notwithstanding the existence of specific air quality standards or emission limits, this

prohibition applies, but is not limited to, any particulate, fume, gas, mist, odor, smoke, vapor,

pollen, toxic or deleterious emission, either alone or in combination with others.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 18 DRAFT

Condition 2-6: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 2-6.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 0NY075-00-0 PARTICULATES

Item 2-6.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Particulate matter(PM) emissions of boilers in emission 

 units U-00010, U-00020 and U-00030 are limited to 0.1 

 lbs/mmbtu. This condition is necessary to ensure 

 compliance with BART requirements under EPA's Regional 

 Haze Program.

 

 The facility shall record the boiler consumption of 

 natural gas and residual oil a daily basis. The compliance

 with the PM emission limit during oil firing shall be 

 verified by performing stack test, using department 

 approved methods, once during the permit term, and for 

 natural gas, by using AP 42 emission factors.

 The compliance deadline, with the emission limitation 

 listed in this condition is January 1, 2014. Compliance 

 with the monitoring, record keeping, or reporting 

 requirements listed in this condition begins on January 1,

 2014. 

Reference Test Method: EPA approved

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

Subsequent reports are due every 6 calendar month(s).

Condition 2-7: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 2-7.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 19 DRAFT

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 2-7.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 This condition applies to boilers under emission units 

 U-00010, U-00020, and U-00030, firing residual oil and 

 natural gas. This condition is necessary to ensure 

 compliance with BART requirements under EPA's Regional 

 Haze Program.

 

 Sulfur content of residual oil used in these boilers shall

 not be greater 0.30 percent by weight. A log of the 

 sulfur content in oil per delivery must be maintained on 

 site. 

 Usage of natural gas ensures that the SO2 emission rate 

 will remain below the EPA's presumptive BART limit of 

 0.15 pounds per million btu.

 Facility shall record the usage of natural gas and 

 residual oil in these boilers . All records shall be kept 

 at the facility for a minimum of five years, and must be 

 available to NYSDEC upon request.

 The compliance deadline, with the emission limitation 

 listed in this condition is January 1, 2014. Compliance 

 with the monitoring, record keeping, or reporting 

 requirements listed in this condition begins on January 1,

 2014.

Reference Test Method: EPA apprpved

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

Subsequent reports are due every 6 calendar month(s).

Condition 2-8: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 2-8.1:

The Compliance Certification activity will be performed for the facility:

The Compliance Certification applies to:

 Emission Unit: U-00010
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 20 DRAFT

 Emission Unit: U-00020

 Emission Unit: U-00030

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 2-8.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 This condition applies to the emission units U-00010, 

 U-00020, and U-00030, firing residual oil and natural 

 gas. This condition is necessary to ensure compliance with

 BART requirements under EPA's Regional Haze Program.

 

 The average NOx emission of boilers in U-00010, U-00020, 

 and U-00030 shall not be greater than 0.15 

 lbs/mmbtu.

 All the records shall be kept at the facility for a 

 minimum of five years, and must be available to NYSDEC 

 upon request.

 The compliance deadline, with the emission limitation 

 listed in this condition is January 1, 2014. Compliance 

 with the monitoring, record keeping, or reporting 

 requirements listed in this condition begins on January 1,

 2014.

Manufacturer Name/Model Number: CEM

Parameter Monitored: OXIDES OF NITROGEN

Upper Permit Limit: 0.15 pounds per million Btus

Reference Test Method: EPA approved

Monitoring Frequency: CONTINUOUS

Averaging Method: 30 DAY ROLLING AVERAGE, ROLLED DAILY

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

Subsequent reports are due every 6 calendar month(s).

Condition 2-9: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (d)

Item 2-9.1:

The Compliance Certification activity will be performed for the Facility.

Item 2-9.2:

Compliance Certification shall include the following monitoring:
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 21 DRAFT

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Control equipment or other emission reduction methods 

 approved by the department as BART must be installed and 

 operating no later than January 1, 2014.

Monitoring Frequency: SINGLE OCCURRENCE

Reporting Requirements: ONCE / BATCH OR MONITORING OCCURRENCE

 ** ** Emission Unit Level  

Condition 53: Process Definition By Emission Unit

 Effective between the dates of 12/06/2006 and Permit Expiration Date

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 53.1(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P01 Source Classification Code: 1-01-004-04

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #6 

 RESIDUAL OIL IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER. A non-hazardous 

 additive may be used to improve combustion.

 

 The facility also may use bio-residual fuel

 which is equivalent to residual fuel oil in

 all respect.

 Emission Source/Control: ES10H - Combustion 

 Design Capacity: 2,102 million Btu per hour

 Emission Source/Control: ES10R - Combustion 

 Design Capacity: 2,102 million Btu per hour

Item 53.2(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P03 Source Classification Code: 1-01-013-02

 Process Description: 

 THIS PROCESS IS THE CO-FIRING OF WASTE 

 FUEL A WITH #6 RESIDUAL OIL AND/OR NATURAL

 GAS IN A TANGENTIALLY FIRED STEAM-ELECTRIC 

 BOILER.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 22 DRAFT

 Emission Source/Control: ES10H - Combustion 

 Design Capacity: 2,102 million Btu per hour

 Emission Source/Control: ES10R - Combustion 

 Design Capacity: 2,102 million Btu per hour

Item 53.3(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00020

 Process: P05 Source Classification Code: 1-01-004-04

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #6 

 RESIDUAL OIL IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER. A non-hazardous 

 additive may be used to improve 

 combustion.

 Emission Source/Control: ES20H - Combustion 

 Design Capacity: 2,085 million Btu per hour

 Emission Source/Control: ES20R - Combustion 

 Design Capacity: 2,085 million Btu per hour

Item 53.4(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00020

 Process: P07 Source Classification Code: 1-01-013-02

 Process Description: 

 THIS PROCESS IS THE CO-FIRING OF WASTE 

 FUEL A WITH #6 RESIDUAL OIL AND/OR NATURAL

 GAS IN A TANGENTIALLY FIRED STEAM-ELECTRIC 

 BOILER.

 Emission Source/Control: ES20H - Combustion 

 Design Capacity: 2,085 million Btu per hour

 Emission Source/Control: ES20R - Combustion 

 Design Capacity: 2,085 million Btu per hour

Item 53.5(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00030

 Process: P09 Source Classification Code: 1-01-004-04

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #6 

 RESIDUAL OIL IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER. A non-hazardous 

 additive may be used to improve combustion.

 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 23 DRAFT

 The facility also may use bio-residual fuel

 which is equivalent to residual fuel oil in

 all respect.

 Emission Source/Control: ES30H - Combustion 

 Design Capacity: 4,689 million Btu per hour

 Emission Source/Control: ES30R - Combustion 

 Design Capacity: 4,689 million Btu per hour

Item 53.6(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00030

 Process: P11 Source Classification Code: 1-01-013-02

 Process Description: 

 THIS PROCESS IS THE CO-FIRING OF WASTE 

 FUEL A WITH #6 RESIDUAL OIL AND/OR NATURAL

 GAS IN A TANGENTIALLY FIRED STEAM-ELECTRIC 

 BOILER.

 Emission Source/Control: ES30H - Combustion 

 Design Capacity: 4,689 million Btu per hour

 Emission Source/Control: ES30R - Combustion 

 Design Capacity: 4,689 million Btu per hour

Item 53.7(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P02 Source Classification Code: 1-01-006-04

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER.

 Emission Source/Control: ES10H - Combustion 

 Design Capacity: 2,102 million Btu per hour

 Emission Source/Control: ES10R - Combustion 

 Design Capacity: 2,102 million Btu per hour

Item 53.8(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P04 Source Classification Code: 5-03-007-01

 Process Description: 

 THIS PROCESS INVOLVES THE INCINERATION OF 

 NON-HAZARDOUS BOILER CHEMICAL CLEANING 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 24 DRAFT

 SOLUTIONS IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER.

 Emission Source/Control: ES10H - Combustion 

 Design Capacity: 2,102 million Btu per hour

 Emission Source/Control: ES10R - Combustion 

 Design Capacity: 2,102 million Btu per hour

Item 53.9(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00020

 Process: P06 Source Classification Code: 1-01-006-04

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER.

 The facility also may use bio-residual fuel

 which is equivalent to residual fuel oil in

 all respect. 

 Emission Source/Control: ES20H - Combustion 

 Design Capacity: 2,085 million Btu per hour

 Emission Source/Control: ES20R - Combustion 

 Design Capacity: 2,085 million Btu per hour

Item 53.10(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00020

 Process: P08 Source Classification Code: 5-03-007-01

 Process Description: 

 THIS PROCESS INVOLVES THE INCINERATION OF 

 NON-HAZARDOUS BOILER CHEMICAL CLEANING 

 SOLUTIONS IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER. 

 Emission Source/Control: ES20H - Combustion 

 Design Capacity: 2,085 million Btu per hour

 Emission Source/Control: ES20R - Combustion 

 Design Capacity: 2,085 million Btu per hour

Item 53.11(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00030

 Process: P10 Source Classification Code: 1-01-006-04

 Process Description: 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 25 DRAFT

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER.

 Emission Source/Control: ES30H - Combustion 

 Design Capacity: 4,689 million Btu per hour

 Emission Source/Control: ES30R - Combustion 

 Design Capacity: 4,689 million Btu per hour

Item 53.12(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00030

 Process: P12 Source Classification Code: 5-03-007-01

 Process Description: 

 THIS PROCESS INVOLVES THE INCINERATION OF 

 NON-HAZARDOUS BOILER CHEMICAL CLEANING 

 SOLUTIONS IN A TANGENTIALLY FIRED 

 STEAM-ELECTRIC BOILER.

 Emission Source/Control: ES30H - Combustion 

 Design Capacity: 4,689 million Btu per hour

 Emission Source/Control: ES30R - Combustion 

 Design Capacity: 4,689 million Btu per hour

Item 53.13(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT001

 Process: P21 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE. 

 Emission Source/Control: ES001 - Combustion 

 Design Capacity: 243 million Btu per hour

Item 53.14(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT004

 Process: P24 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 26 DRAFT

 Emission Source/Control: ES004 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.15(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT004

 Process: P25 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES004 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.16(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT004

 Process: P26 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES004 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.17(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT005

 Process: P29 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES005 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.18(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 27 DRAFT

 Emission Unit: U-CT005

 Process: P30 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES005 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.19(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT005

 Process: P31 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES005 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.20(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT006

 Process: P34 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES006 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.21(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT006

 Process: P35 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 28 DRAFT

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES006 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.22(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT006

 Process: P36 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES006 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.23(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT007

 Process: P39 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES007 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.24(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT007

 Process: P40 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 29 DRAFT

 Emission Source/Control: ES007 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.25(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT007

 Process: P41 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES007 - Combustion 

 Design Capacity: 235 million Btu per hour

Item 53.26(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT008

 Process: P44 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES008 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.27(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT008

 Process: P45 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES008 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.28(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT008

 Process: P46 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 30 DRAFT

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES008 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.29(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT009

 Process: P47 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES009 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.30(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT009

 Process: P48 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES009 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.31(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT009

 Process: P49 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 31 DRAFT

 Emission Source/Control: ES009 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.32(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT010

 Process: P50 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES010 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.33(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT010

 Process: P51 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES010 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.34(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT010

 Process: P52 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES010 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.35(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 32 DRAFT

 Emission Unit: U-CT011

 Process: P53 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE

 NATURAL GAS IN A COMBUSTION TURBINE.

 Emission Source/Control: ES011 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.36(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT011

 Process: P54 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES011 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.37(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT011

 Process: P55 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING.

 Emission Source/Control: ES011 - Combustion 

 Design Capacity: 255 million Btu per hour

Item 53.38(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S1

 Process: P22 Source Classification Code: 2-01-001-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 33 DRAFT

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S1 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.39(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S1

 Process: P23 Source Classification Code: 2-02-009-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S1 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.40(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S4

 Process: P27 Source Classification Code: 2-02-001-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S4 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.41(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S4

 Process: P28 Source Classification Code: 2-02-009-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 34 DRAFT

 Emission Source/Control: ES0S4 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.42(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S5

 Process: P32 Source Classification Code: 2-02-001-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S5 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.43(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S5

 Process: P33 Source Classification Code: 2-02-009-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S5 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.44(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S6

 Process: P37 Source Classification Code: 2-02-001-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S6 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.45(From Mod 0):
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 35 DRAFT

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S6

 Process: P38 Source Classification Code: 2-02-009-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S6 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.46(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S7

 Process: P42 Source Classification Code: 2-02-001-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S7 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.47(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT0S7

 Process: P43 Source Classification Code: 2-02-009-02

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A DIESEL ENGINE. THIS 

 ENGINE IS USED TO START THE ASSOCIATED 

 COMBUSTION TURBINE. DURING EACH START-UP 

 THE ENGINE OPERATES FOR LESS THAN 15 

 MINUTES.

 Emission Source/Control: ES0S7 - Combustion 

 Design Capacity: 430 horsepower (mechanical)

Item 53.48(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT201

 Process: P56 Source Classification Code: 2-01-002-01
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 36 DRAFT

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utalized 

 for NOx reduction, as required. Throughputs listed under 

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.

 Emission Source/Control: ES21A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES21B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.49(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT201

 Process: P57 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit. 

 Emission Source/Control: ES21A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES21B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.50(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT201

 Process: P58 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 37 DRAFT

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit. 

 Emission Source/Control: ES21A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES21B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.51(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT202

 Process: P59 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under 

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.

 Emission Source/Control: ES22A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES22B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.52(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT202

 Process: P60 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 38 DRAFT

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES22A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES22B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.53(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT202

 Process: P61 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES22A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES22B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.54(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT203

 Process: P62 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 39 DRAFT

 Emission Source/Control: ES23A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES23B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.55(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT203

 Process: P63 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES23A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES23B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.56(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT203

 Process: P64 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs listed

 under each process are intended to be 

 examples of possible unit utilization. 

 Actual operation to be in accordance with 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 40 DRAFT

 the emission limitations identified in the 

 Emission Unit portion of this permit. 

 Emission Source/Control: ES23A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES23B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.57(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT204

 Process: P65 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under 

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.

 Emission Source/Control: ES24A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES24B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.58(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT204

 Process: P66 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES24A - Combustion 

 Design Capacity: 262 million Btu per hour
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 41 DRAFT

 Emission Source/Control: ES24B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.59(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT204

 Process: P67 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES24A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES24B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.60(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT301

 Process: P68 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under 

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.

 Emission Source/Control: ES31A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES31B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.61(From Mod 0):
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 42 DRAFT

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT301

 Process: P69 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES31A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES31B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.62(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT301

 Process: P70 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES31A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES31B - Combustion 

 Design Capacity: 262 million Btu per hour
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 43 DRAFT

Item 53.63(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT302

 Process: P71 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.

 Emission Source/Control: ES32A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES32B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.64(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT302

 Process: P72 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs listed

 under each process are intended to be 

 examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES32A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES32B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.65(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT302
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 44 DRAFT

 Process: P73 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs listed

 under each process are intended to be 

 examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES32A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES32B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.66(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT303

 Process: P74 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit. 

 Emission Source/Control: ES33A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES33B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.67(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT303

 Process: P75 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 45 DRAFT

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES33A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES33B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.68(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT303

 Process: P76 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utalized for NOx 

 reduction, as required. Thruputs listed 

 under each process are intended to be 

 examples of possible unit utalization. 

 Actual operation be be inaccordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES33A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES33B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.69(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT304

 Process: P77 Source Classification Code: 2-01-002-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF PIPELINE NATURAL GAS IN
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 46 DRAFT

 A COMBUSTION TURBINE. Inlet water spray may be utilized 

 for NOx reduction, as required. Throughputs listed under

 each process are intended to be examples of possible unit 

 utilization. Actual operation to be in accordance with 

 the emission limitations identified in the Emission Unit 

 portion of this permit.

 Emission Source/Control: ES34A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES34B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.70(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT304

 Process: P78 Source Classification Code: 2-01-001-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #2 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs listed

 under each process are intended to be 

 examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES34A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES34B - Combustion 

 Design Capacity: 262 million Btu per hour

Item 53.71(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-CT304

 Process: P79 Source Classification Code: 2-01-009-01

 Process Description: 

 THIS PROCESS IS THE COMBUSTION OF #1 

 DISTILLATE OIL IN A COMBUSTION TURBINE. IN 

 ORDER TO IMPROVE COMBUSTION A FUEL ADDITIVE

 MAY BE MIXED WITH THE DISTILLATE OIL PRIOR 

 TO COMBUSTION. IN ADDITION, WHEN FUEL OIL 

 IS STORED FOR EXTENDED PERIODS, A BIOCIDE 
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 47 DRAFT

 MAY BE ADDED TO PREVENT FOULING. Inlet 

 water spray may be utilized for NOx 

 reduction, as required. Throughputs 

 listed under each process are intended to 

 be examples of possible unit utilization. 

 Actual operation to be in accordance with 

 the emission limitations identified in the 

 Emission Unit portion of this permit.

 Emission Source/Control: ES34A - Combustion 

 Design Capacity: 262 million Btu per hour

 Emission Source/Control: ES34B - Combustion 

 Design Capacity: 262 million Btu per hour

Condition 2-10: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (f)

Item 2-10.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00010

Item 2-10.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The emission limits in this permit for NOx, SO2, and/or 

 PM10 established under Part 249 are based on New York's 

 Best Available Retrofit Technology (BART) Rule (6 NYCRR 

 Part 249), are effective on the date of this permit's 

 issuance, and are state-enforceable. Federal 

 enforceability of these facility-specific requirements is 

 effective on the date on which these emission limits, as 

 submitted to EPA as a revision to New York State's 

 Implementation Plan for Regional Haze, are published in 

 the Federal Register.

Monitoring Frequency: SEMI-ANNUALLY

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

Subsequent reports are due every 6 calendar month(s).

Condition 2-11: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (f)

Item 2-11.1:
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 48 DRAFT

The Compliance Certification activity will be performed for:

 Emission Unit: U-00020

Item 2-11.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The emission limits in this permit for NOx, SO2, and/or 

 PM10 established under Part 249 are based on New York's 

 Best Available Retrofit Technology (BART) Rule (6 NYCRR 

 Part 249), are effective on the date of this permit's 

 issuance, and are state-enforceable. Federal 

 enforceability of these facility-specific requirements is 

 effective on the date on which these emission limits, as 

 submitted to EPA as a revision to New York State's 

 Implementation Plan for Regional Haze, are published in 

 the Federal Register.

Monitoring Frequency: SEMI-ANNUALLY

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

Subsequent reports are due every 6 calendar month(s).

Condition 2-12: Compliance Certification

 Effective for entire length of Permit

 Applicable Federal Requirement:6 NYCRR 249.3 (f)

Item 2-12.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00030

Item 2-12.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The emission limits in this permit for NOx, SO2, and/or 

 PM10 established under Part 249 are based on New York's 

 Best Available Retrofit Technology (BART) Rule (6 NYCRR 

 Part 249), are effective on the date of this permit's 

 issuance, and are state-enforceable. Federal 

 enforceability of these facility-specific requirements is 

 effective on the date on which these emission limits, as 

 submitted to EPA as a revision to New York State's 

 Implementation Plan for Regional Haze, are published in 

 the Federal Register.

Monitoring Frequency: SEMI-ANNUALLY
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 49 DRAFT

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

Subsequent reports are due every 6 calendar month(s).
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 50 DRAFT

 STATE ONLY ENFORCEABLE CONDITIONS

 ** ** Facility Level ****

 NOTIFICATION OF GENERAL PERMITTEE OBLIGATIONS

This section contains terms and conditions which are not federally enforceable. Permittees

may also have other obligations under regulations of general applicability

Item A: General Provisions for State Enforceable Permit Terms and

 Condition - 6 NYCRR Part 201-5

 Any person who owns and/or operates stationary sources 

 shall operate and maintain all emission units and any 

 required emission control devices in compliance with all 

 applicable Parts of this Chapter and existing laws, and 

 shall operate the facility in accordance with all 

 criteria, emission limits, terms, conditions, and 

 standards in this permit. Failure of such person to 

 properly operate and maintain the effectiveness of such 

 emission units and emission control devices may be 

 sufficient reason for the Department to revoke or deny a 

 permit.

 The owner or operator of the permitted facility must 

 maintain all required records on-site for a period of five

 years and make them available to representatives of the 

 Department upon request. Department representatives must 

 be granted access to any facility regulated by this 

 Subpart, during normal operating hours, for the purpose of

 determining compliance with this and any other state and 

 federal air pollution control requirements, regulations or

 law.

 STATE ONLY APPLICABLE REQUIREMENTS

The following conditions are state applicable requirements and are not subject to 

compliance certification requirements unless otherwise noted or required 

 under 6 NYCRR Part 201.

Condition 85: Contaminant List

 Effective between the dates of 12/06/2006 and Permit Expiration Date

 Applicable State Requirement:ECL 19-0301

Item 85.1:

Emissions of the following contaminants are subject to contaminant specific requirements in this

permit(emission limits, control requirements or compliance monitoring conditions).

 CAS No: 000630-08-0

 Name: CARBON MONOXIDE
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 51 DRAFT

 CAS No: 007446-09-5

 Name: SULFUR DIOXIDE

 CAS No: 0NY075-00-0

 Name: PARTICULATES

 CAS No: 0NY210-00-0

 Name: OXIDES OF NITROGEN

Condition 2-13: Unavoidable noncompliance and violations

 Effective for entire length of Permit

 Applicable State Requirement:6 NYCRR 201-1.4

Item 2-13.1:

At the discretion of the commissioner a violation of any applicable emission standard for

necessary scheduled equipment maintenance, start-up/shutdown conditions and malfunctions or

upsets may be excused if such violations are unavoidable. The following actions and

recordkeeping and reporting requirements must be adhered to in such circumstances.

(a) The facility owner and/or operator shall compile and maintain records of all

equipment maintenance or start-up/shutdown activities when they can be expected to result in an

exceedance of any applicable emission standard, and shall submit a report of such activities to

the commissioner's representative when requested to do so in writing or when so required by a

condition of a permit issued for the corresponding air contamination source except where

conditions elsewhere in this permit which contain more stringent reporting and notification

provisions for an applicable requirement, in which case they supercede those stated here. Such

reports shall describe why the violation was unavoidable and shall include the time, frequency

and duration of the maintenance and/or start-up/shutdown activities and the identification of air

contaminants, and the estimated emission rates. If a facility owner and/or operator is subject to

continuous stack monitoring and quarterly reporting requirements, he need not submit reports for

equipment maintenance or start-up/shutdown for the facility to the commissioner's

representative.

(b) In the event that emissions of air contaminants in excess of any emission standard

in 6 NYCRR Chapter III Subchapter A occur due to a malfunction, the facility owner and/or

operator shall report such malfunction by telephone to the commissioner's representative as soon

as possible during normal working hours, but in any event not later than two working days after

becoming aware that the malfunction occurred. Within 30 days thereafter, when requested in

writing by the commissioner's representative, the facility owner and/or operator shall submit a

written report to the commissioner's representative describing the malfunction, the corrective

action taken, identification of air contaminants, and an estimate of the emission rates. These

reporting requirements are superceded by conditions elsewhere in this permit which contain

reporting and notification provisions for applicable requirements more stringent than those

above.

(c) The Department may also require the owner and/or operator to include in reports

described under (a) and (b) above an estimate of the maximum ground level concentration of

each air contaminant emitted and the effect of such emissions depending on the deviation of the

malfunction and the air contaminants emitted.

(d) In the event of maintenance, start-up/shutdown or malfunction conditions which
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 52 DRAFT

result in emissions exceeding any applicable emission standard, the facility owner and/or

operator shall take appropriate action to prevent emissions which will result in contravention of

any applicable ambient air quality standard. Reasonably available control technology, as

determined by the commissioner, shall be applied during any maintenance, start-up/shutdown or

malfunction condition subject to this paragraph.

(e) In order to have a violation of a federal regulation (such as a new source performance

standard or national emissions standard for hazardous air pollutants) excused, the specific

federal regulation must provide for an affirmative defense during start-up, shutdowns,

malfunctions or upsets.

Condition 2-14: Visible Emissions Limited

 Effective for entire length of Permit

 Applicable State Requirement:6 NYCRR 211.2

Item 2-14.1:

Except as permitted by a specific part of this Subchapter and for open fires for which a restricted

burning permit has been issued, no person shall cause or allow any air contamination source to

emit any material having an opacity equal to or greater than 20 percent (six minute average)

except for one continuous six-minute period per hour of not more than 57 percent opacity.
 

Permit ID: 2-6304-00024/00035 Facility DEC ID: 2630400024

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Changes Only Page 53 DRAFT