Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data fro

fuel burning power plants and which test methods were used to do so for cases where the test methods are not 

supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in t

if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 se

runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one 

one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required. All cells that are shaded in green are populated using drop-down lists. You do not need to 

cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. 

resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls 

(example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksh

2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. 

spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission 

results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or c

family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter bot

Hg+2, or if the Ontario-Hydro Method was used, you would need to enter Hg0, HgP, and Hg

Volatile Organic HAP and Speciated Semi-Volatile Organic HAP worksheets allow you to use a drop

Constituent field to define as many records as needed to record each HAP that you have results for. General ins

follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample.

2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop-downs in the Fuel Type Selection 

You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more sa

then enter an input rate of zero. 

2. Please enter the unit of measure using the drop down provided.

3. Please enter the test method used to determine the fuel input rate.

4. Please provide any other information that you feel may be important in the Other Supporting Information fie

Emission Data
1. Some constituents ask for the emission rate results of each run in two different units of measure, while other

If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) 

ppmvd @ 7% O2(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both.

2. Please provide the test method used. This may or may not match the example given in the Test Method Used 

Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010).

3. Please provide any other information that you feel may be important in the Other Supporting Information fie

4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for p

enter these data.
nformation about emission data from fossil 

ses where the test methods are not currently 

nly be used if the method is not in the ERT or 

T. You must complete at least 3 separate 

sheet is intended to be used for one boiler of 

copies of this spreadsheet. Fields shaded in 

down lists. You do not need to populate 

rmation worksheet. Please name each 

nit_[BoilerID]_EmisTestMethods.xls 

ler on the Boiler Information worksheet. 

ent family required for this analysis. On each 

fuel input information, and emission test 

d depending on the constituent or constituent 

Mercury requires that you enter both Hg0 and 

, HgP, and Hg+2. However, both the Speciated 

low you to use a drop-down provided in the 

at you have results for. General instructions 

er Supporting Information field.

downs in the Fuel Type Selection field. 

fuel types entered in one or more samples, 

he Other Supporting Information field.
erent units of measure, while others do not. 

b/MMBtu (Pounds per million BTU) and 

, you are required to provide both.

mple given in the Test Method Used field. 

ethod (ex. U.S. EPA Method 0010).

he Other Supporting Information field.

 method you are entering data for please also 
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2
Control Device Configuraton

Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR
lectronic ICR
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time
Measured Value (ppm)

Test End Date Test End Time
Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

CO Emission Test Results
Test Method Comments lb/mmBtu ppmdv @ 7% O2

Calculated Emission Rate
Steam Output (1000 lb/hr) Total Heat Input 

(mmBtu/hr) Flue Gas Moisture (%)
Flue Gas CO

2

 (%) Flue Gas O

2

 (%) Flue Gas Flow Rate 

(dscfm)
Fuel Input Rate Fuel Type

Flue Gas Temperature (F)

Fuel #1
Units of Measure Measurement Method Fuel Input Rate

Fuel #1
Fuel Type Units of Measure Measurement Method

Fuel #2
Fuel Input Rate Fuel Type Units of Measure

Fuel #3
Measurement Method Fuel Input Rate Fuel Type

Fuel #4
Units of Measure Measurement Method

Fuel #4

Other Supporting 

Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

Test End Time

Formaldehyde Emission Test Results
Test Method 

Comments lb/mmBtu ppmdv @ 7% O2

Steam Output (1000 

lb/hr)

Total Heat Input 

(mmBtu/hr)

Calculated Emission Rate
Fuel Input 

Rate Fuel Type Units of Measure

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

Moisture (%)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas Flow 

Rate (dscfm)
Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Fuel #2 Fuel #3
Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time
Measured Value (ppm) Basis (Wet or Dry) Test End Date Test End Time

Methane Emission T
Test Method Used Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments lb/mmBtu

Methane Emission Test Results Calculated Emission Rate
ppmdv @ 7% O2

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

lated Emission Rate

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)
Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Measurement 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Flue Gas 

Temperat

ure (F)

Fuel #1 Fuel #2
Measurement 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Measurement 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Fuel #3 Fuel #4
Measurement 

Method

Other Supporting 

Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used Test End Time

SO2 Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments lb/mmBtu ppmdv @ 7% O

2

Calculated Emission Rate Steam Output 

(1000 lb/hr)
Fuel Input 

Rate Fuel Type

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Temperature 

(F)

Fuel #1
Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type

Fuel #1 Fuel #2 Fuel #3
Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
Other Supporting Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time
Please note QA/QC documentation starting in Column "AI"

Measured Value 

(μg/dscm) Basis (Wet or Dry) Test End Time

Total Vapor Phase Mercury Em

Test End Date
 starting in Column "AI"

Test Method Used Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments (lb/mmBtu)

Total Vapor Phase Mercury Emission Test Results

Steam Output 

(1000 lb/hr)
Fuel Input Rate

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature (F)

Flue Gas 

Moisture 

(%)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

CO2 (%)
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #1 Fuel #2
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
 QA/QC Documentation

Trap ID Section 1 

Mass (ng)

Section 2 

Mass (ng)

Total 

Mass (ng)

Initial 

Spike 

(ng)

Total NonSpike (ng)

Other Supporting Information
Sample 

Volume 

(dscm)

Volume 

Difference (%)

Volume Diff. 

Limit

Breaktrough 

(%)

Breaktrough 

Limit

Concentration 

(μg/dscm) Trap ID

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

≤20% of field 

recovery test

≤ 10% of 

Section 1 Hg 

mass for Hg 

conc. >1 

μg/dscm: or ≤ 

20% of Section 

Trap #1
Section 1 

Mass

Section 2 

Mass

Total 

Mass

Initial 

Spike

Total NonSpikeSample 

Volume

Volume 

Difference (%)

Volume Diff. 

Limit

≤20% of field 

recovery test

Trap #2
Breaktrough (%) Breaktrough 

Limit

Concentration 

(μg/dscm) Abs. diff. RD (%) Limit Crec

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

Paired Trap Agreement (RD) Measured Spik

≥10 % RD mass 

for Hg conc. >1 

μg/dscm: or 

≤20% RD or ≤0.2 

μg/dscm abs.diff. 

for Hg conc. ≤1 

≤ 10% of Section 

1 Hg mass for 

Hg conc. >1 

μg/dscm: or ≤ 

20% of Section 1 

for Hg conc.≤1 
R (%) by 

Run Ravg (%) Limit

Average 

Recovery, 

between 85 and 

115%

Measured Spike Recovery ( R )

#DIV/0!
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time
Measured Hg

0

 Value 

(μg/dscm)

Measured Hg+2 Value 

(μg/dscm)

Test End Date Test End Time
Measured HgP

 Value 

(μg/dscm)

Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

Total Vapor Phase Mercury Emission Test Results
Test Method 

Comments

Total Mercury 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)

Flue Gas 

CO

2

 (%)
Fuel Input Rate Fuel Type Units of 

Measure

Measurement 

Method

Fuel #1 Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)
Fuel Input Rate Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Other Supporting Information

Fuel #4
Measured 

Value 

(μg/m3)

Basis Test Method Used 

Data Flag 

(ADL, 

BDL, 

DDL)

Front 

Half 

Mass 

(ng)

Back Half 

Mass 

(ng)

Total 

Mass 

(ng)

Test 

Method 

Comments

lb/mmBtu ppmdv @ 

7% O2

Fuel 

Input 

Rate

Fuel Type Units of 

Measure Measurement Method

Benzene 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 4.9E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 138.6 0.0 138.6 4.15E-06 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Bromochloromethane 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 0.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL 0.0 0.0 0.0 0.00E+00 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Bromodichloromethane 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 2.9E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 8.1 0.0 8.1 2.43E-07 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Bromomethane 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 5.3E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 150.0 0.0 150.0 4.49E-06 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Carbon Disulfide 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 7.3E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 208.0 0.0 208.0 6.23E-06 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Carbon Tetrachloride 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 2.1E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 5.9 0.0 5.9 1.77E-07 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Chloroform 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 1.8E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 45.0 6.7 51.7 1.55E-06 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Methyl chloride 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 3.4E+01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 958.0 0.0 958.0 2.87E-05 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Dichlorodifluoromethane 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 9.4E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 26.7 0.0 26.7 8.00E-07 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

2-Hexanone 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 2.3E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 39.0 26.0 65.0 1.95E-06 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Methylene Chloride 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 1.6E+03 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 996.0 43,333.3 44,329.3 1.33E-03 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Styrene 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 1.3E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 3.7 0.0 3.7 1.11E-07 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Tetrachloroethylene 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 8.8E-02 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 2.5 0.0 2.5 7.49E-08 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Toluene 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 1.6E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 41.2 5.3 46.5 1.39E-06 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Trichloroethylene 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 0.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL 0.0 0.0 0.0 0.00E+00 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Trichlorofluoromethane 1 5/10/2010 9:15 AM 5/10/2010 11:15 AM 6.5E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 18.4 0.0 18.4 5.51E-07 580 783 10.3 13.32 5.87 170151 193 783 bituminous MMBtu/hr boiler efficiency calculation

Benzene 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 3.9E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 122.5 0.0 122.5 3.34E-06 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Bromochloromethane 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 1.7E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 0.0 5.3 5.3 1.46E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Bromodichloromethane 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 2.8E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 8.9 0.0 8.9 2.43E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Bromomethane 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 8.1E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 253.0 0.0 253.0 6.90E-06 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Carbon Disulfide 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 2.0E+01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 625.6 0.0 625.6 1.71E-05 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Carbon Tetrachloride 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 4.8E-02 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 1.5 0.0 1.5 4.09E-08 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Chloroform 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 2.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 55.0 6.3 61.3 1.67E-06 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Methyl chloride 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 3.3E+01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 1,031.8 0.0 1,031.8 2.82E-05 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Dichlorodifluoromethane 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 6.3E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 19.6 0.0 19.6 5.35E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

2-Hexanone 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 1.1E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 35.0 0.0 35.0 9.55E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Methylene Chloride 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 1.3E+03 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 213.0 40,000.0 40,213.0 1.10E-03 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Styrene 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 1.5E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 4.8 0.0 4.8 1.31E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Tetrachloroethylene 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 5.5E-02 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 0.0 1.7 1.7 4.73E-08 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Toluene 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 1.1E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 32.9 0.0 32.9 8.98E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Trichloroethylene 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 4.3E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 13.6 0.0 13.6 3.71E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Trichlorofluoromethane 2 5/10/2010 11:58 AM 5/10/2010 1:58 PM 3.1E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 9.6 0.0 9.6 2.62E-07 577 769 10.4 13.54 5.96 169729 201 769 bituminous MMBtu/hr boiler efficiency calculation

Benzene 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 2.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 50.6 1.0 51.6 1.80E-06 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Bromochloromethane 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 2.0E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 0.0 5.0 5.0 1.75E-07 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Bromodichloromethane 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 2.2E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 5.7 0.0 5.7 1.99E-07 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Bromomethane 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 3.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 76.4 0.0 76.4 2.67E-06 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Carbon Disulfide 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 6.1E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 157.0 0.0 157.0 5.49E-06 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Carbon Tetrachloride 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 1.1E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 2.7 0.0 2.7 9.45E-08 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Chloroform 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 1.5E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 33.6 6.0 39.6 1.39E-06 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Methyl chloride 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 8.4E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 215.6 0.0 215.6 7.54E-06 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Dichlorodifluoromethane 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 3.8E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 9.6 0.0 9.6 3.36E-07 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

2-Hexanone 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 8.6E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 0.0 22.0 22.0 7.70E-07 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Methylene Chloride 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 1.6E+03 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 142.0 40,000.0 40,142.0 1.40E-03 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Styrene 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 0.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL 0.0 0.0 0.0 0.00E+00 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Tetrachloroethylene 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 4.3E-02 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 1.1 0.0 1.1 3.85E-08 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Toluene 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 6.8E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 10.6 6.7 17.3 6.04E-07 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Trichloroethylene 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 0.0E+00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL 0.0 0.0 0.0 0.00E+00 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Trichlorofluoromethane 3 5/10/2010 2:40 PM 5/10/2010 4:40 PM 2.3E-01 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DDL 5.8 0.0 5.8 2.03E-07 519 701 10.2 12.85 6.63 169042 198 701 bituminous MMBtu/hr boiler efficiency calculation

Flue Gas 

O2 (%)

Flue Gas 

Flow 

Rate 

(scfm)

Flue Gas 

Temperat

ure (F)

Calculated Emission Fuel #1

Steam 

Output 

(1000 

lb/hr)

Total 

Heat 

Input 

(mmBtu/

hr)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

Compound 

(use drop down to define for as many rows as 

needed)

Run Number Test Start 

Date

Test Start 

Time

Test End 

Date

Test End 

Time
EIA Facility Code

Facility 

Name Boiler ID

10384 Edgecombe Power Station 2

Speciated Semi-Volatile Organic HAP Emission Data

Benzoic Acid 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Bis(2-ethylhexyl) phthalate 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Di-n-octyl phthalate 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Acenaphthene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Acenaphthylene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Chrysene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Fluoranthene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Fluorene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

2-Methylnaphthalene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Naphthalene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Phenanthrene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Pyrene 1 5/10/2010 9:15 AM 5/10/2010 11:31 AM

Benzoic Acid 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Acenaphthene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Acenaphthylene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Chrysene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Fluoranthene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Fluorene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

2-Methylnaphthalene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Naphthalene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Phenanthrene 2 5/10/2010 11:59 AM 5/10/2010 2:07 PM

Benzoic Acid 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Acenaphthene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Benzo(g,h,i)perylene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Benzo(a)pyrene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Benzo(e)pyrene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Chrysene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Fluoranthene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Fluorene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

2-Methylnaphthalene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Naphthalene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Phenanthrene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Pyrene 3 5/10/2010 2:41 PM 5/10/2010 4:48 PM

Compound 

(use drop down to define for as many rows as 

needed)

Run 

Number

Test Start 

Date

Test Start 

Time

Test End 

Date

Test End 

Time







Footnote

s:

* Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses

** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses

*** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses

Measured 

Value 

(μg/m3)

Basis 

(Wet or 

Dry)

Test 

Method 

Used 

Data Flag 

(ADL, 

BDL, 

DDL)

Front 

Half 

mass* 

(ng)

Back Half 

mass* 

(ng)

Condens

ate 

Mass*** 

(ng)

Total 

Composit

e (ng)

Test 

Method 

Comment

s

lb/mmBtu

2.13E+01 Dry U.S. EPA Method 0010 with SW DDL 0.0-846 Method 8270D 52000.0 0.0 52000 1.81E-05

1.68E+00 Dry U.S. EPA Method 0010 with SW DDL 4100.0-846 Method 8270D 0.0 0.0 4100 1.43E-06

4.06E+00 Dry U.S. EPA Method 0010 with SW DDL 9900.0-846 Method 8270D 0.0 0.0 9900 3.44E-06

6.55E-03 Dry U.S. EPA Method 0010 with SW DDL 16.0-846 Method 8270D 0.0 0.0 16 5.57E-09

1.27E-03 Dry U.S. EPA Method 0010 with SW DDL 3.1-846 Method 8270D 0.0 0.0 3.1 1.08E-09

1.47E-03 Dry U.S. EPA Method 0010 with SW DDL 2.7-846 Method 8270D 0.0 0.9 3.6 1.25E-09

5.00E-03 Dry U.S. EPA Method 0010 with SW DDL 5.7-846 Method 8270D 6.5 0.0 12.2 4.24E-09

6.15E-03 Dry U.S. EPA Method 0010 with SW DDL 15.0-846 Method 8270D 0.0 0.0 15 5.22E-09

9.42E-02 Dry U.S. EPA Method 0010 with SW DDL 210.0-846 Method 8270D 20.0 0.0 230 8.00E-08

3.24E-01 Dry U.S. EPA Method 0010 with SW DDL 790.0-846 Method 8270D 0.0 0.0 790 2.75E-07

1.15E-02 Dry U.S. EPA Method 0010 with SW DDL 28.0-846 Method 8270D 0.0 0.0 28 9.74E-09

4.51E-03 Dry U.S. EPA Method 0010 with SW DDL 0.0-846 Method 8270D 11.0 0.0 11 3.83E-09

1.62E+01 Dry U.S. EPA Method 0010 with SW DDL 0.0-846 Method 8270D 40000.0 0.0 40000 1.38E-05

4.86E-03 Dry U.S. EPA Method 0010 with SW DDL 12.0-846 Method 8270D 0.0 0.0 12 4.15E-09

1.22E-03 Dry U.S. EPA Method 0010 with SW DDL 3.0-846 Method 8270D 0.0 0.0 3 1.04E-09

8.10E-04 Dry U.S. EPA Method 0010 with SW DDL 2.0-846 Method 8270D 0.0 0.0 2 6.92E-10

3.97E-03 Dry U.S. EPA Method 0010 with SW DDL 3.1-846 Method 8270D 6.7 0.0 9.8 3.39E-09

6.48E-03 Dry U.S. EPA Method 0010 with SW DDL 9.9-846 Method 8270D 6.1 0.0 16 5.54E-09

9.32E-02 Dry U.S. EPA Method 0010 with SW DDL 230.0-846 Method 8270D 0.0 0.0 230 7.96E-08

4.05E-01 Dry U.S. EPA Method 0010 with SW DDL 1000.0-846 Method 8270D 0.0 0.0 1000 3.46E-07

8.51E-03 Dry U.S. EPA Method 0010 with SW DDL 21.0-846 Method 8270D 0.0 0.0 21 7.27E-09

1.53E+01 Dry U.S. EPA Method 0010 with SW DDL 0.0-846 Method 8270D 39000.0 0.0 39000 1.37E-05

3.06E-03 Dry U.S. EPA Method 0010 with SW DDL 7.8-846 Method 8270D 0.0 0.0 7.8 2.74E-09

3.18E-03 Dry U.S. EPA Method 0010 with SW DDL 8.1-846 Method 8270D 0.0 0.0 8.1 2.84E-09

9.03E-04 Dry U.S. EPA Method 0010 with SW DDL 2.3-846 Method 8270D 0.0 0.0 2.3 8.07E-10

1.49E-03 Dry U.S. EPA Method 0010 with SW DDL 3.8-846 Method 8270D 0.0 0.0 3.8 1.33E-09

8.24E-04 Dry U.S. EPA Method 0010 with SW DDL 2.1-846 Method 8270D 0.0 0.0 2.1 7.37E-10

6.91E-03 Dry U.S. EPA Method 0010 with SW DDL 8.3-846 Method 8270D 9.3 0.0 17.6 6.18E-09

6.08E-03 Dry U.S. EPA Method 0010 with SW DDL 8.3-846 Method 8270D 7.2 0.0 15.5 5.44E-09

5.93E-02 Dry U.S. EPA Method 0010 with SW DDL 130.0-846 Method 8270D 0.0 21.0 151 5.30E-08

3.02E-01 Dry U.S. EPA Method 0010 with SW DDL 590.0-846 Method 8270D 0.0 180.0 770 2.70E-07

7.07E-03 Dry U.S. EPA Method 0010 with SW DDL 18.0-846 Method 8270D 0.0 0.0 18 6.32E-09

6.67E-03 Dry U.S. EPA Method 0010 with SW DDL 0.0-846 Method 8270D 17.0 0.0 17 5.97E-09

Semi-Volatile Organic HAP Emission Test Results Calculated Emission 







olvent rinses

ondenser solvent rinses

solvent rinses

ppmdv @ 

7% O2

Fuel 

Input 

Rate

Fuel Type

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

580 783 10.288 13.32 5.87 170161.4 193.03 783 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

577 769 10.363 13.54 5.96 169798.2 200.82 769 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

520 701 10.247 12.85 6.63 168962.7 198.4 701 bituminous

Flue Gas 

O2 (%)

Flue Gas 

Flow 

Rate 

(scfm)

Flue Gas 

Temperat

ure (F)

Calculated Emission 

Steam 

Output 

(1000 

lb/hr)

Total 

Heat 

Input 

(mmBtu/h

r)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)







Units of 

Measure

Measurement Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Measure

ment 

Method

Fuel 

Input 

Rate

Fuel Type

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

MMBtu/hr boiler efficiency calculation

Fuel #1 Fuel #2 Fuel #3







Units of 

Measure

Measure

ment 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Measure

ment 

Method

Fuel #4 Other 

Supporti

ng 

Informati

on

Fuel #3







EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

Hydrogen Cyanide Emission Test Results

Test End Time
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used Test End Time

Hydrogen Chloride Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

 Test Results

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

Hydrogen Flouride Emission Test Results

Test End Time
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

Test Results

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time
Measured NO (ppm) Test End Date Test End Time
Measured NO2

 (ppm) Basis (Wet or Dry) Test Method Used 

NOX Emission Test Results
Data Flag (ADL, BDL, DDL) Test Method Comments (lb/mmBtu)

Total NOX Calculated Emission Rate
ppmdv @ 7% O2

Flue Gas 

Moisture (%)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

 Calculated Emission Rate Steam Output 

(1000 lb/hr)

Total Heat Input 

(mmBtu/hr)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

10384 Edgecombe Power Station 2

Run Number Test Start Date Test Start Time
Total Dissolved Solids 

(mg solids/liter)

Total Suspended Solids 

(mg solids/liter)

Test End Date Test End Time
Test Method Used Data Flag (ADL, 

BDL, DDL)

Constisuent Emission Test Results
Test Method Comments Fuel Input Rate

Flue Gas 

Temperat

ure (F)

Flue Gas 

Flow Rate 

(dscfm)

Steam Output 

(1000 lb/hr)

Total Heat Input 

(mmBtu/hr)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate

Fuel #1 Fuel #2
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
Other Supporting Information





Fuel

anthracite

bituminous

subbituminous

lignite

coal refuse (culm or gob)

No.2 Fuel Oil (distillate)

No.6 Fuel Oil (residual or bunker C)

synfuel

petroleum coke

other

Relative to Control Device

Upstream

Downstream

Fuel Input Units of Measure

MMBtu/hr

standard cubic feet per minute (scfm)

gallon/minute

lb/hour

ton/day

Exhaust Flow Rate Units of Measure

acfm

dscfm

Exhaust Temperature Units of Measure

deg C

deg F

Test Method Used for Fuel Input Rate

F-Factor

gas fuel meter

boiler efficiency calculation

Other

CO Test Method

U.S. EPA Method 10A

U.S. EPA Method 10B

Formaldehyde Test Method

U.S. EPA Method 320
U.S. EPA Method 0011

U.S. EPA Method 316

CH4 Test Method

U.S. EPA Method 18

U.S. EPA Method 320

SO2 Test Method

U.S. EPA Method 6

Hg Test Method

U.S. EPA Method 30B

Speciated Volatile Organic HAP Method

U.S. EPA Method 0031 with SW-846 Method 8260B

U.S. EPA Method 0031/TO-15

Speciated Semi-Volatile Organic HAP Method

U.S. EPA Method 0010 with SW-846 Method 8270C

U.S. EPA Method 0010 with SW-846 Method 8270D

HCN Test Method

U.S. EPA Conditional Test Method 033 (CTM-033)

U.S. EPA Method 320

CARB 426

U.S. EPA Method 26A-Mod

O2/CO2 Test Method

U.S. EPA Method 3B

NOX Test Method

U.S. EPA Method 7

U.S. EPA Method 7A

U.S. EPA Method 7B

U.S. EPA Method 7C

U.S. EPA Method 7D

TDS/TSS Test Method

Standard Test Method for Filterable and Nonfilterable Matter in Water ASTM D5907

Standard Methods of the Examination of Water and Wastewater Method 2540B

Control Configuration

Listed (by boiler) in Question 16 (page 17) of the questionnaire

Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR
Hg Ontario Hydro Test Method

ASTM Method D6784

HCL Test Methods

U.S. EPA Method 320

U.S. EPA Method 26

HF Test Methods

U.S. EPA Method 320

U.S. EPA Method 26

Basis

Wet

Dry


Constituent CAS

Methyl chloride 74-87-3

1,1,2-Trichloroethane 79-00-5

1,1-Dimethylhydrazine 57-14-7

1,2,4-Trichlorobenzene 120-82-1

1,2-Dibromo-3-chloropropane 96-12-8

1,2-Epoxybutane (1,2-butylene oxide) 106-88-7

1,2-Propyleneimine (2-methylaziridine) 75-55-8

1,3-Butadiene 106-99-0

1,3-Dichloropropene 542-75-6

1,3-Propane sultone 1120-71-4

1,4-Dichlorobenzene (p-) 106-46-7

1,4-Dioxane (1,4-Diethylene oxide) 123-91-1

2,2,4-Trimethyl pentane 540-84-1

2-Nitropropane 79-46-9

Acetaldehyde 75-07-0

Acetonitrile (cyanomethane) 75-05-8

Acetophenone 98-86-2

Acrolein (2-propenal) 107-02-8

Acrylamide 79-06-1

Acrylic acid 79-10-7

Acrylonitrile (2-propenenitrile) 107-13-1

Allyl chloride (3-chloropropene) 107-05-1

Aniline (aminobenzene) 62-53-3

Benzene 71-43-2

Benzyl chloride (a-chlorotoluene) 100-44-7

Beta-Propiolactone 57-57-8

Bis(2-Chloroethyl)ether 111-44-4

Bromochloromethane 74-97-5

Bromodichloromethane 75-27-4

Carbon disulfide 75-15-0

Carbon tetrachloride 56-23-5

Carbonyl sulfide 463-58-1

Bromomethane 74-83-9

Chloroacetic acid 79-11-8

Chlorobenzene 108-90-7

Chloroform 67-66-3

Chloromethyl methyl ether 107-30-2

Chloroprene (2-chloro-1,3-butadiene) 126-99-8

Cresylic acid (cresol isomer mixture) 1319-77-3

Cumene (isopropylbenzene) 98-82-8

Dichlorodifluoromethane 75-71-8

Diethyl sulfate 64-67-5

Dimethyl sulfate 77-78-1

Dimethylcarbamyl chloride 79-44-7

Epichlorohydrin (1-chloro-2,3-epoxy

propane) 106-89-8

Ethyl acrylate 140-88-5

Ethyl carbamate (urethane) 51-79-6

Ethyl chloride 75-00-3

Speciated Volatile Organic HAPs
Ethylbenzene 100-41-4

Ethylene dibromide (1,2-dibromoethane) 106-93-4

Ethylene dichloride (1,2-dichloroethane) 107-06-2

Ethylene oxide 75-21-8

Ethyleneimine (aziridine) 151-56-4

Ethylidene dichloride (1,1-dichloroethane) 75-34-3

Formaldehyde 50-00-0

Hexachlorobutadiene 87-68-3

Hexachloroethane 67-72-1

Hexane 110-54-3

Isophorone 78-59-1

1, 1, 2, 2-Tetrachloroethane 79-34-5

Methanol 67-56-1

Methyl bromide 74-83-9.

Methyl chloroform (1,1,1-trichloroethane) 71-55-6

Methyl ethyl ketone (2-butanone) 78-93-3

Methyl iodide 74-88-4

Methyl isobutyl ketone (hexone) 108-10-1

Methyl isocyanate 624-83-9

Methyl methacrylate 80-62-6

Methyl tert-butyl ether 1634-04-4

Methylene chloride 75-09-2

Methylhydrazine 60-34-4

m-Xylene 108-38-3

N,N-Dimethylaniline 100-23-2

N,N-Dimethylformamide 68-12-2

Nitrobenzene 98-95-3

N-Nitrosodimethylamine 62-75-9

N-Nitrosomorpholine 59-89-2

2-Hexanone 591-78-6

o-Cresol 95-48-7

o-Xylene 95-47-6

Phenol 108-95-2

Phosgene 75-44-5

Propionaldehyde 123-38-6

Propylene dichloride (1,2-dichloropropane) 78-87-5

Propylene oxide 75-56-9 

p-Xylene 106-42-3

Styrene 100-42-5

Trichlorofluoromethane 75-69-4

Tetrachloroethylene 127-18-4

Toluene 108-88-3

Trichloroethylene 79-01-6

Triethylamine 121-44-8

Vinyl acetate 108-05-04

Vinyl bromide 593-60-2

Vinyl chloride (chloroethene) 75-01-4

Vinylidene chloride 75-35-4

Xylenes (isomer & mixtures) 1330-20-7

lectronic ICR








Speciated Semi-volatile Organic HAPs

Constituent CAS

2-Methylnaphthalene 91-57-6

Acenaphthene 83-32-9

Acenaphthylene 208-96-8

Anthracene 120-12-7

Benzo(a)anthracene 56-55-3

Benzo(a)pyrene 50-32-8

Benzo(b)fluoranthene 205-99-2

Benzo(e)pyrene 192-97-2

Benzo(g,h,i)perylene 191-24-2

Benzo(k)fluoranthene 207-08-9

Chrysene 218-01-9

Dibenzo(a,h)anthracene 53-70-3

Fluoranthene 206-44-0

Fluorene 86-73-7

Indeno(1,2,3-cd)pyrene 193-39-5

Naphthalene 91-20-3

Perylene 77392-71-3

Phenanthrene 85-01-8

Pyrene 129-00-0

Acetophenone 98-86-2

2-Acetylaminofluorene 53-96-3

1-Acetyl-2-thiourea 591-08-2

Aldrin 309-00-2

2-Aminoanthraquinone 117-79-3

Aminoazobenzene 60-09-3

4-Aminobiphenyl 92-67-1

3-Amino-9-ethylcarbazole 132-32-1

Anilazine 101-05-3

Aniline 62-53-3

o-Anisidine 90-04-0

Aramite 140-57-8

Aroclor 1016 12674-11-2

Aroclor 1221 11104-28-2

Aroclor 1232 11141-16-5

Aroclor 1242 53469-21-9

Aroclor 1248 12672-29-6

Aroclor 1254 11097-69-1

Aroclor 1260 11096-82-5

Azinphos-methyl 86-50-0

Barban 101-27-9

Benzidine 92-87-5

Benzoic acid 65-85-0

p-Benzoquinone 106-51-4

Benzyl alcohol 100-51-6

α-BHC 319-84-6

β-BHC 319-85-7

δ-BHC 319-86-8

γ-BHC (Lindane) 58-89-9
Bis(2-chloroethoxy)methane 111-91-1

Bis(2-chloroethyl) ether 111-44-4

Bis(2-chloroisopropyl) ether 39638-32-9

Bis(2-ethylhexyl) phthalate 117-81-7

4-Bromophenyl phenyl ether 101-55-3

Bromoxynil 1689-84-5

Butyl benzyl phthalate 85-68-7

Captafol 2425-06-1

Captan 133-06-2

Carbaryl 63-25-2

Carbofuran 1563-66-2

Carbophenothion 786-19-6

Chlordane (NOS) 57-74-9

Chlorfenvinphos 470-90-6

4-Chloroaniline 106-47-8

Chlorobenzilate 510-15-6

5-Chloro-2-methylaniline 95-79-4

4-Chloro-3-methylphenol 59-50-7

3-(Chloromethyl)pyridine hydrochloride 6959-48-4

1-Chloronaphthalene 90-13-1

2-Chloronaphthalene 91-58-7

2-Chlorophenol 95-57-8

4-Chloro-1,2-phenylenediamine 95-83-0

4-Chloro-1,3-phenylenediamine 5131-60-2

4-Chlorophenyl phenyl ether 7005-72-3

Coumaphos 56-72-4

p-Cresidine 120-71-8

Crotoxyphos 7700-17-6

2-Cyclohexyl-4,6-dinitro-phenol 131-89-5

4,4'-DDD 72-54-8

4,4'-DDE 72-55-9

4,4'-DDT 50-29-3

Demeton-O 298-03-3

Demeton-S 126-75-0

Diallate (cis or trans) 2303-16-4

2,4-Diaminotoluene 95-80-7

Dibenz(a,j)acridine 224-42-0

Dibenzofuran 132-64-9

Dibenzo(a,e)pyrene 192-65-4

1,2-Dibromo-3-chloropropane 96-12-8

Di-n-butyl phthalate 84-74-2

Dichlone 117-80-6

1,2-Dichlorobenzene 95-50-1

1,3-Dichlorobenzene 541-73-1

1,4-Dichlorobenzene 106-46-7

3,3'-Dichlorobenzidine 91-94-1

2,4-Dichlorophenol 120-83-2

2,6-Dichlorophenol 87-65-0

Dichlorovos 62-73-7

Dicrotophos 141-66-2

Dieldrin 60-57-1
Diethyl phthalate 84-66-2

Diethylstilbestrol 56-53-1

Diethyl sulfate 64-67-5

Dimethoate 60-51-5

3,3'-Dimethoxybenzidine 119-90-4

Dimethylaminoazobenzene 60-11-7

7,12-Dimethylbenz(a)-anthracene 57-97-6

3,3'-Dimethylbenzidine 119-93-7

α,α-Dimethylphenethylamine 122-09-8

2,4-Dimethylphenol 105-67-9

Dimethyl phthalate 131-11-3

1,2-Dinitrobenzene 528-29-0

1,3-Dinitrobenzene 99-65-0

1,4-Dinitrobenzene 100-25-4

4,6-Dinitro-2-methylphenol 534-52-1

2,4-Dinitrophenol 51-28-5

2,4-Dinitrotoluene 121-14-2

2,6-Dinitrotoluene 606-20-2

Dinocap 39300-45-3

Dinoseb 88-85-7

Diphenylamine 122-39-4

5,5-Diphenylhydantoin 57-41-0

1,2-Diphenylhydrazine 122-66-7

Di-n-octyl phthalate 117-84-0

Disulfoton 298-04-4

Endosulfan I 959-98-8

Endosulfan II 33213-65-9

Endosulfan sulfate 1031-07-8

Endrin 72-20-8

Endrin aldehyde 7421-93-4

Endrin ketone 53494-70-5 X X ND X X 53494-70-5

EPN 2104-64-5

Ethion 563-12-2

Ethyl carbamate 51-79-6

Ethyl methanesulfonate 62-50-0

Famphur 52-85-7

Fensulfothion 115-90-2

Fenthion 55-38-9

Fluchloralin 33245-39-5

2-Fluorobiphenyl (surr) 321-60-8

2-Fluorophenol (surr) 367-12-4

Heptachlor 76-44-8

Heptachlor epoxide 1024-57-3

Hexachlorobenzene 118-74-1

Hexachlorobutadiene 87-68-3

Hexachlorocyclopentadiene 77-47-4

Hexachloroethane 67-72-1

Hexachlorophene 70-30-4

Hexachloropropene 1888-71-7

Hexamethylphosphoramide 680-31-9

Hydroquinone 123-31-9

Isodrin 465-73-6

Isophorone 78-59-1

Isosafrole 120-58-1
Kepone 143-50-0

Leptophos 21609-90-5

Malathion 121-75-5

Maleic anhydride 108-31-6

Mestranol 72-33-3

Methapyrilene 91-80-5

Methoxychlor 72-43-5

3-Methylcholanthrene 56-49-5

4,4'-Methylenebis (2-chloroaniline) 101-14-4

4,4'-Methylenebis(N,N-dimethylaniline) 101-61-1

Methyl methanesulfonate 66-27-3

Methyl parathion 298-00-0

2-Methylphenol 95-48-7

3-Methylphenol 108-39-4

4-Methylphenol 106-44-5

Mevinphos 7786-34-7

Mexacarbate 315-18-4

Mirex 2385-85-5

Monocrotophos 6923-22-4

Naled 300-76-5

1,4-Naphthoquinone 130-15-4

1-Naphthylamine 134-32-7

2-Naphthylamine 91-59-8

Nicotine 54-11-5

5-Nitroacenaphthene 602-87-9

2-Nitroaniline 88-74-4

3-Nitroaniline 99-09-2

4-Nitroaniline 100-01-6

5-Nitro-o-anisidine 99-59-2

Nitrobenzene 98-95-3

4-Nitrobiphenyl 92-93-3

Nitrofen 1836-75-5

2-Nitrophenol 88-75-5

4-Nitrophenol 100-02-7

5-Nitro-o-toluidine 99-55-8

Nitroquinoline-1-oxide 56-57-5

N-Nitrosodi-n-butylamine 924-16-3

N-Nitrosodiethylamine 55-18-5

N-Nitrosodimethylamine 62-75-9

N-Nitrosodiphenylamine 86-30-6

N-Nitrosodi-n-propylamine 621-64-7

N-Nitrosomethylethylamine 10595-95-6

N-Nitrosomorpholine 59-89-2

N-Nitrosopiperidine 100-75-4

N-Nitrosopyrrolidine 930-55-2

Octamethyl pyrophosphoramide 152-16-9

4,4'-Oxydianiline 101-80-4

Parathion 56-38-2

Pentachlorobenzene 608-93-5

Pentachloronitrobenzene 82-68-8

Pentachlorophenol 87-86-5

Phenacetin 62-44-2

Phenobarbital 50-06-6

Phenol 108-95-2

1,4-Phenylenediamine 106-50-3
Phorate 298-02-2

Phosalone 2310-17-0

Phosmet 732-11-6

Phosphamidon 13171-21-6

Phthalic anhydride 85-44-9

2-Picoline (2-Methylpyridine) 109-06-8

Piperonyl sulfoxide 120-62-7

Pronamide 23950-58-5

Propylthiouracil 51-52-5

Resorcinol 108-46-3

Safrole 94-59-7

Strychnine 57-24-9

Sulfallate 95-06-7

Terbufos 13071-79-9

1,2,4,5-Tetrachlorobenzene 95-94-3

2,3,4,6-Tetrachlorophenol 58-90-2

Tetrachlorvinphos 961-11-5

Tetraethyl dithiopyrophosphate 3689-24-5

Tetraethyl pyrophosphate 107-49-3

Thionazine 297-97-2

Thiophenol (Benzenethiol) 108-98-5

Toluene diisocyanate 584-84-9

o-Toluidine 95-53-4

Toxaphene 8001-35-2

1,2,4-Trichlorobenzene 120-82-1

2,4,5-Trichlorophenol 95-95-4

2,4,6-Trichlorophenol 88-06-2

Trifluralin 1582-09-8

2,4,5-Trimethylaniline 137-17-7

Trimethyl phosphate 512-56-1

1,3,5-Trinitrobenzene 99-35-4

Tris(2,3-dibromopropyl) phosphate 126-72-7

Tri-p-tolyl phosphate 78-32-0

O,O,O-Triethyl phosphorothioate 126-68-1