---------

- - **-~--**

**-~** ------

------ **--------~-**

**------** SENT

BY EMAIL

TO: ( SteiPK@jea.com

) In the Matter

of

an Application

for Permit

by: JEA Paul Steinbrecher,

P .E. 4377 Heckscher

Drive Jacksonville,

Florida

32202

Florida Department

of Environmental

Protection Bob Martinez

Center 2600

Blair

Stone

Road Tallahassee,

Florida 32399-2400 PA File

No. FL0001031-007-IW1S Duval County

Rick

Scott Governor Jennifer

Carroll Lt. Governor Herschel

T. Vinyard

Jr. Secretary Northside Generating

Station

and

St. Johns

River Power

Park NPDES

Permit

No. FL0001031 NOTICE

OF PERMIT ISSUANCE Enclosed

i

s Permit Number

FLOOOO

1031

to JEA authorizing

wastewater

discharge

from Units

1

, 2, and

3 of the Northside Generating

Station

and Units

1 and

2 the

St. Johns

River Power

Park

to the

St. Johns

River,

a Class III marine

water,

issued

under Section 403.0885,

Florida Statutes,

and DEP

Rule 62-620,

Florida Administrative Code. Monitoring requirements

under

this permit

are effective

on the first

day

of the second

month following permit issuance.

Until

such

time,

the permittee

shall continue

to monitor

and report

in accordance

with previously effective

permit requirements,

if any. Any party

to this order (permit)

has

the right

to seek judicial

review

of the permit

under Section

120.68, Florida Statutes,

by

the filing

of

a Notice

of Appeal

under

Rules

9

. 110

and

9 .190, Florida

Rules

of Appellate Procedure,

with

the Clerk

of the Department

of Environmental

Protection,

Office

of General Counsel,

Mail Station

35, 3900 Commonwealth

Boulevard, Tallahassee,

Florida 32399-3000

and

by filing

a copy

of the notice of appeal accompanied

by

the applicable

filing

fees

with

the appropriate

district

court

of appeal.

The notice

of appeal

must

b

e filed within

thirty

days

aft

er this notice

is filed

with

the clerk

of the Department. Executed

in Tallahassee,

Florida.

Director Division

of Water Resource Management 2600

Blair

Stone

Road Tallahassee,

FL 32399-2400JEANorthsideGeneratingStationandSt.JohnsRiverPowerParkCERTIFICATEOFSERVICEPage2of2NPDESPermitNo.FL0001031TheundersigneddulydesignateddeputyclerkherebycertifiesthatthisNOTICEOFPERMITandallcopiesweremailedbycertifiedmailbeforethecloseofbusinesson05,O'f-I1..tothelistedpersons.[ClerkStamp]FILINGANDACKNOWLEDGMENTFILED,onthisdate,undersection120.52(7),FloridaStatutes,withthedesignatedDepartmentClerk,receiptofwhichisherebyacknowledged.tlA.05·oq.,z_ClerkDateCopiesfurnishedbyemailto:MarkNuhfer,NPDESandBiosolidsPermitsSection,EPARegion4,Atlanta,GA(Nuhfer.Mark@epa.gov)Karrie-JoShell,PowerPlantNPDESPermits,EPARegion4 (Shell.Karrie-Jo@epamail.epa.gov)President,JacksonvilleCityCouncil(Joost@coj.net)FloridaFishandWildlifeConservationCommission,ConservationPlanningServices(FWCConservationPlanningServices@myfwc.com)U.S.Fish&WildlifeService(JimValade@fws.gov)U.S.ArmyCorpsofEngineers(James.J.McAdams@usace.army.mil)AnnHarvey,Esq.,Earthjustice(aharvey@earthjustice.org)EdCordova,P.E.,JEA(corded@jea.com)MelissaLong,P.E.,DEPJacksonville(Melissa.M.Long@dep.state.fl.us)DungVo,P.E.,DEPJacksonville(Dung.Vo@dep.state.fl.us)JeffMartin,P.E.,DEPJacksonville(Jeff.Martin@dep.state.fl.us)RobertMartin,P.G.,DEPJacksonville(Robert.L.Martin@dep.state.fl.us)TomRauth,DEPJacksonville(Tom.Rauth@dep.state.fl.us)CindyMulkey,DEPTallahassee(Cindy.Mulkey@dep.state.fl.us)JustinWolfe,Esq.,DEPTallahassee(Justin.G.Wolfe@dep.state.fl.us)STATEOFFLORIDAINDUSTRIALWASTEWATERFACILITYPERMITPERMITTEE:JEARESPONSffiLEOFFICIAL:PaulSteinbrecher,P.E.4377HeckscherDriveJacksonville,Florida32226(904)665-8729FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerPark4377HeckscherDriveJacksonville,FL32226-3033DuvalCountyPERMITNUMBER:FILENUMBER:ISSUANCEDATE:EXPIRATIONDATE:Latitude:30°24'59.63"NLongitude:81°33'10.31"WFL0001031-007{Major)FLOOOl031-007-IWlSMay9,2012May8,2017ThispermitisissuedundertheprovisionsofChapter403,FloridaStatutes(F.S.),andapplicablerulesoftheFloridaAdministrativeCode(F.A.C.)andconstitutesauthorizationtodischargetowatersofthestateundertheNationalPollutantDischargeEliminationSystem.Thispermitdoesnotconstituteauthorizationtodischargewastewaterotherthanasexpresslystatedinthispermit.Theabovenamedpermitteeisherebyauthorizedtooperatethefacilitiesinaccordancewiththedocumentsattachedheretoandspecificallydescribedasfollows:FACILITYDESCRIPTION:TheNorthsideGeneratingStation(NGS)andSt.JohnsRiverPowerPark(SJRPP)facilitiesareconsideredtobeasingle"facility"forindustrialwastewaterpermittingpurposes.Thefacilityisanelectricgeneratingplantwithatotalnameplateratingof2,433megawatts(MW).Thefacilityconsistsofgeneratingfacilitieslocatedontwoadjacentplantsites.Collectively,theseplantsconsistoftwodual-fired(petroleumcoke/coal)circulatingfluidizedbedsteamturbine-generatorunits(NGSUnits1and2);onedual-fired(oil/gas)steamturbine-generatorunit(NGSUnit3);fourdiesel-firedcombustionturbine-generatorunits(NGSCTs3,4,5,and6);andtwobitumouscoal,andpetroleumcokeandnaturalgas-firedsteamturbine-generatorunits(SJRPPUnits1and2).EachoftheNGScirculatingfluidizedbedunitsisequippedwithSelectiveNon-CatalyticReduction(SNCRs)andeachoftheSJRPPunitsisequippedwithselectivecatalyticreduction(SCR)systemsandammoniainjectionsystemstoreducenitrogenoxidesandsulfuricacidmist.SJRPPUnits1and2arealsoregulatedundertheFloridaElectricalPowerPlantSitingAct(LicenseNo.PA81-13).WASTEWATERTREATMENT:Once-throughnon-contactcoolingwater(OTCW)fortheNGSisdrawnfromtheSt.JohnsRiverandtreatedwithsodiumhypochloriteorsodiumbromide.OTCWsystemdischargesamaximumflowof827MGDbacktotheSt.JohnsRiveraftercirculatingthroughthecondensersascoolingwater.Lowvolumewastes(LVW),includingairpre-heaterandboilerwashwater,boilerblowdown,demineralizerregenerationwaste,powerblockstormdrains,boilerareadrains,flyandbedashmanagementareas,limeslakerseals,carbonpurifierbackwash,equipmentareafloordrains,by-productsarealeachate,stormwaterrunoff,fuelstoragedomesump,containingcoalandpetcokecondensatecollectionwithequipmentwash,filterbackwash,andotherwastestreamsaretreatedintheChemicalWasteTreatmentSystem(CWTS),whichhasamaximumdesigncapacityof3.0MGD.TheCWTSconsistsoftwolinedsurgebasinswithoil/waterseparators,limeaddition,rapidmixingbasins,flocculationbasins,limesettlingponds,re-carbonationandacidinjectionevaporation/percolationponds,andasludgedryingarea.Adailyaverageof0.2304MGDofreclaimedwaterfromtheJEADistrictIIWaterReclamationFacility isusedascirculatorpumpsealwaterandisdischargedtothecoolingwaterdischargebasin.Make-upwaterfortheSJRPPnaturaldraftcoolingtowersiswithdrawnfromtheNGSdischargechannelandtheblowdownfromthecoolingtowersisreturnedtotheNGSdischargechanneljustdownstreamoftheSJRPPintakestructure.Themake-PERMITTEE:JEAFACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FLOOO1031-007(Major)May8,2017upwaterischlorinatedduringcirculationinthecoolingtowers.Lowvolumewastes,metalcleaningwastesandotherwastestreamsaretreatedintheCentralWastewaterTreatmentFacility(CWTF)bychemicalconditioningandprecipitation,clarificationandcoagulation,multimediaflltrationandneutralization.ThetotalnitrogenwasteloadallocationforthisfacilityisaddressedundertheJEAAggregateTNTMDLPermit(FL0620564).REUSEORDISPOSAL:NorthsideGeneratingStation:SurfaceWaterDischargeD-001:Anexisting827MGDDailyMaximumFlowpermitteddischargetothemaindischargecanalandthencetotheSt.JohnsRiver,ClassIIIMarineWaters(WBID2213B).Thepointofdischargeislocatedapproximatelyatlatitude30°24'57"N,longitude81°33'5"W.SurfaceWaterDischargeD-010:AnexistingemergencyoverflowtoSanCarlosCreek,ClassIIIMarineWater(WBID2216).Thepointofdischargeislocatedapproximatelyatlatitude30°25'20"N,longitude81°33'2"W.SurfaceWaterDischargeD-Oll:AnexistingemergencyoverflowtoSanCarlosCreek(WBID2216).Thepointofdischargeislocatedapproximatelyatlatitude30°25'14"N,longitude81o33'7"W..LandApplicationR-001:AnexistingdischargetoClassIIgroundwaterbylandapplicationsystemconsistingofevaporation/percolationponds,sludgeponds,limesettlingponds,coalpilestoragearea,petcokepilestoragearea,andEZBaseProductionFacility.St.JohnsRiverPowerParkStormwaterDischargeD-002:AnexistingpermitteddischargetoBrownsCreek(WBID2209).Thepointofdischargeislocatedapproximatelyatlatitude30°25'36"N,longitude81°32'39"W.SurfaceWaterDischargeD-004:AnexistingpermitteddischargetoBrownsCreek,ClassIIIMarineWaters(WBID2209).Thepointofdischargeislocatedapproximatelyatlatitude30°25'35"N,longitude81o32'46"W.SurfaceWaterDischargeD-009:AnexistingpermitteddischargetoBrownsCreek,ClassIIIMarineWaters(WBID2209).Thepointofdischargeislocatedapproximatelyatlatitude30°26'2"N,longitude81°32'40"W.InternalOutfallI-001:Anexisting77MGDDailyMaximumFlowpermitteddischargetotheNGSencloseddischargebasin,andthencetotheSt.John'sRiver,ClassIIIMarineWaters(WBID2213B).Thepointofdischargeislocatedapproximatelyatlatitude30°24'56"N,longitude81°33'5"W.InternalOutfallI-005:Anexistingpermitteddischargetothemaindischargecanal.InternalOutfallI-006:AnexistingpermitteddischargetothemaindischargecanalviaI-005.INACCORDANCEWITH:Thelimitations,monitoringrequirementsandotherconditionssetforthinthisCoverSheetandPartIthroughPartIXonpages1through34ofthispermit.2PERMITTEE:JEAFACILITY:NorthsideGeneratingStationandSt.JolmsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FLOOO1031-007(Major)MayS,2017I.EFFLUENTLIMITATIONSANDMONITORINGREQUIREMENTSA.SurfaceWaterDischarges1.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeProcessWastewatersinNGSdischargechannelfromOutfallD-001totheSt.JolmsRiver.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitorinl!;RequirementsMonitoringMax/FrequencyofSampleSiteParameterUnitsMinLimitStatisticalBasisAnalvsisTypeNumberNotesFlowMGDMaxReportDailyMaximumHourlyPumpLogsFLW-1MaxReoortMonthlvAverageMaxReportDailyMaximumTemperature,Water(Intake)DegFMinReportDailyMinimumContinuousRecorder1INT-IMaxReoortMonthlvAveral!;eMax104DailyMaximumTemperature,WaterDegFMinReportDailyMinimumContinuousRecorder1EFF-1MaxReportMonthlyAveral!;eTemp.Diff.betweenIntakeMax19DailyMaximumandDischargeDegFMinReportDailyMinimumContinuousCalculatedEFF-1MaxReportMonthlyAveragepHMin6.5DailyMinimumMonthlyGrabEFF-lCs.u.Max8.5DailyMaximumOxidants,TotalResidualmg/LMax0.1DailyMaximumWeeklyRecorder1EFF-1SeeI.A.7Max0.1MonthlyAveral!;eand8TRODischargeTimemin/Max120DailyMaximumDaily;24hoursCalculatedEFF-1dayMax120MonthlyAveral!;eAluminum,TotalRecoverableug/LMaxReportDailyMaximumSemi-annually24-hrTPCEFF-1CMaxReoortMonthlyAveral!;eArsenic,TotalRecoverableug/LMax36DailyMaximumSemi-annually24-hrTPCEFF-lCMax36MonthlyAverageChromium,TotalRecoverableug/LMaxReportDailyMaximumSemi-annually24-hrTPCEFF-1CMaxReoortMonthlvAverageCopper,TotalRecoverableug/LMaxReportDailyMaximumMonthly24-hrTPCEFF-ICMaxReportMonthlvAverageINT-IIron,TotalRecoverablemg/LMaxReportDailyMaximumMonthly24-hrTPCEFF-1CMaxReportMonthlyAverageINT-IMercury,TotalRecoverableug/LMax0.025DailyMaximumMonthly24-hrTPCEFF-ICMax0.025MonthlyAverageINT-ILead,TotalRecoverableug/LMaxReportDailyMaximumSemi-annually24-hrTPCEFF-1CMaxReportMonthlyAverageNickel,TotalRecoverableug/LMaxReportDailyMaximumSemi-annually24-hrTPCEFF-ICMaxReportMonthlyAverageSelenium,TotalRecoverableug/LMax71DailyMaximumMonthly24-hrTPCEFF-ICMax71MonthlyAveral!;eINT-1Silver,TotalRecoverableug/LMaxReportDailyMaximumSemi-annually24-hrTPCEFF-ICMaxReportMonthlyAveral!;eZinc,TotalRecoverableug/LMaxReportDailyMaximumSemi-annually24-hrTPCEFF-ICMaxReportMonthlyAveral!;eSpecificConductanceumhos/MaxReportDailyMaximumMonthly24-hrTPCEFF-ICemMaxReportMonthlyAveral!;e1Metersshallbecalibratedatleastonceayearinaccordancewiththemanufacturerrecommendations.Calibrationrecordsshallbemaintainedon-siteinaccordancewithConditionV.IIofthispermit.3PERMITTEE:JEAPERMITNUMBER:FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:FL0001031-007(Major)MayS,2017EffluentLimitationsMonitoringRequirementsMonitoringMax/FrequencyofSampleSiteParameterUnitsMinLimitStatisticalBasisAnalysisTypeNumberChronicWholeEffluentToxicity,7-DayIC25percentMin100SingleSampleQuarterly24-hrTPCEFF-IC(Mysidopsisbahia)ChronicWholeEffluentToxicity,7-DayIC25percentMin100SingleSampleQuarterly24-hrTPCEFF-IC(Menidiaberyllina)2.EftluentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.A.I.andasdescribedbelow:MonitoringSiteNumberDescriptionofMonitoringSiteFLW-1Pumplogs.INT-IInfluentsamplingfromtheintakebasin.NotesSeeI.A.I4SeeI.A.l4EFF-1CombineddischargeofUnits1,2,and3priortoco-minglingwiththedischargefromSt.JohnsRiverPowerPark.EFF-ICFivefootstandpipeoffofthedischargepipelocatedonNorthsideGeneratingStationpropertyjustsouthoftheHeckscherDrivebridgebeforeitgoesintotheSt.JohnsRiver.3.ThermaldischargefromthisfacilityshallbeincompliancewithRule62-302.520(1),F.A.C.4.Thedailymaximumtemperatureshallbethehighestdailyaveragetemperaturethroughoutthemonth.Thedailyaveragetemperatureisthearithmeticaverageofallvaluesobtainedforanycalendarday.Themonthlyaveragetemperatureisthesumofallthedailyvaluesmeasuredduringacalendarmonthonwhichdailydischargeismeasured,dividedbythenumberofdailydischargedmeasuredduringthatmonth(thearithmeticmeanofthedailyvalues).Thetemperatureriseiscalculatedasthedifferencebetweenthedailyaveragetemperatureofthedischargeandthedailyaveragetemperatureoftheintake.5.Dischargeofintakescreenbackwashwaterispermittedwithoutlimitationormonitoringrequirements,exceptthatthereshallbenodischargeofvisibleoilsheen.6.Continuousmonitoringofintake(INT-I)anddischargetemperature(EFF-1)andtemperatureriseasrequiredbyConditionI.A.I.forOutfallD-001shallbeatleastonceperhour.7.TotalResidualOxidants{TRO)meansthevalueobtainusingtestingproceduresforTotalResidualChlorine(TRC)foundin40CFR136.3.8.IfcontinuousmonitoringequipmentforTROisnotoperableduringanydischargeperiod,thepermitteeshallcollectmultiplegrabsamplesandanalyzethosesamplesbyothermeansthatmeettherequirementsofPermitConditionsI.D.land2andshallspecifythemethodintheDischargeMonitoringReport.MultiplegrabsamplesforTROshallconsistofgrabsamplescollectedatthebeginningoftheperiodofchlorinationdischarge,andonceevery15minutes,thereafter.Inaddition,onegrabsampleshallbecollectedattheendoftheperiodofoxidantdischarge.9.GrabsamplesforTROmonitoringisrequiredonlyduringtimeswhensodiumhypochloriteand/orsodiumbromideisaddedtothecondensercoolingwatersystem.TotalResidualOxidantsshallnotexceed0.1mg/LasmonitoredatEFF-1.InnocaseshallTRObedischargedfromanyunitformorethantwo hoursperdayperunit.NotmorethanoneunitshalldischargeTROatanyonetime.4PERMITTEE:JEAPERMITNUMBER:FLOOO1031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:10.Thedischargeshallnotcontaincomponentsthatsettletoformputrescentdepositsorfloatasdebris,scum,oil,orothermatter.[62-302.500(1)(a)]11.Thepermitteeshallmaintainthecurrentintakethrough-screenvelocitysuchthattheexistingmaximumvelocityisnotexceeded.[C.W.A.316(b)]12.ThepermitteeshallmaintaincurrenttravelingscreenpracticesatUnits1,2,and3soastoassurethatthescreensarecycledtwiceduringeach24hoursofcontinuousoperationunlessprecludedbyrepair/maintenancerequirements.[C.W.A.316(b)]13.ThepermitteeshalldevelopaplaninaccordancewiththescheduleinConditionVl.3tohelpreturnlivefish,shellfish,andotheraquaticorganismscollectedortrappedontheintakescreenstotheirnaturalhabitat.OthermaterialshallberemovedfromtheintakescreensanddisposedofinaccordancewithallexistingFederal,Stateand/orLocallawsandregulationsthatapplytowastedisposal.Suchmaterialshallnotbereturnedtothereceivingwaters.[C.W.A.316(b)]14.ThepermitteeshallcomplywiththefollowingrequirementstoevaluatechronicwholeeffluenttoxicityofthedischargefromoutfallD-001.a.EffluentLimitation(1)Inanyroutineoradditionalfollow-uptestforchronicwholeeffluenttoxicity,the25percentinhibitionconcentration(IC25)shallnotbelessthan100%effluent.[Rules62-302.530(61)and62-4.241(1)(b),F.A.C.}(2)Foracutewholeeffluenttoxicity,the96-hourLC50shallnotbelessthan100%effluentinanytest.[Rules62-302.500(1)(a)4.and62-4.241(1)(a),F.A.C.]b.MonitoringFrequency(1)Routinetoxicitytestsshallbeconductedonceeverythreemonths,thefrrststartingwithin60daysoftheissuancedateofthispermitandlastingforthedurationofthispermit.(2)Uponcompletionoffourconsecutive,validroutineteststhatdemonstratecompliancewiththeeffluentlimitationin14.a.(1)above,thepermitteemaysubmitawrittenrequesttotheDepartmentforareductioninmonitoringfrequencytoonceeverysixmonths.Therequestshallincludeasummaryofthedataandthecompletebioassaylaboratoryreportsforeachtestusedtodemonstratecompliance.TheDepartmentshallactontherequestwithin45daysofreceipt.ReductionsinmonitoringshallonlybecomeeffectiveupontheDepartment'swrittenconfirmationthatthefacilityhascompletedfourconsecutivevalidroutineteststhatdemonstratecompliancewiththeeffluentlimitationin14.a.(1)above.(3)IfatestwithinthesequenceofthefourisdeemedinvalidbasedontheacceptancecriteriainEPA-821-R-02-014,butisreplacedbyarepeatvalidtestinitiatedwithin21daysafterthelastdayoftheinvalidtest,theinvalidtestwillnotbecountedagainsttherequirementforfourconsecutivevalidtestsforthepurposeofevaluatingthereductionofmonitoringfrequency.c.SamplingRequirements(1)Foreachroutinetestoradditionalfollow-uptestconducted,atotalofthree24-hourcompositesamplesoffinaleffluentshallbecollectedandusedinaccordancewiththesamplingprotocoldiscussedinEPA-821-R-02-014,Section8.(2)Thefirstsampleshallbeusedtoinitiatethetest.TheremainingtwosamplesshallbecollectedaccordingtotheprotocolandusedasrenewalsolutionsonDay3(48hours)andDay5(96hours)ofthetest.(3)Samplesforroutineandadditionalfollow-uptestsshallnotbecollectedonthesameday.d.TestRequirements(1)RoutineTests:Allroutinetestsshallbeconductedusingacontrol(0%effluent)andaminimumoffivetestdilutions:100%,50%,25%,12.5%,and6.25%finaleffluent.(2)Thepermitteeshallconduct7-daysurvivalandgrowthchronictoxicitytestswithamysidshrimp,Americamysis(Mysidopsis)bahia,Method1007.0,andaninlandsilverside,Menidiaberyllina,Method1006.0,concurrently.(3)Alltestspecies,proceduresandqualityassurancecriteriausedshallbeinaccordancewithShort-termMethodsforEstimatingtheChronicToxicityofEffluentsandReceivingWaterstoMarineand5PERMITTEE:FACILITY:JEAPERMITNUMBER:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:FLOOO1031-007(Major)MayS,2017EstuarineOrganisms,3rdEdition,EPA-821-R-02-014.AnydeviationofthebioassayproceduresoutlinedhereinshallbesubmittedinwritingtotheDepartmentforreviewandapprovalpriortouse.Intheeventtheabovemethodisrevised,thepermitteeshallconductchronictoxicitytestinginaccordancewiththerevisedmethod.(4)Thecontrolwateranddilution waterusedshallbeartificialseasaltsasdescribedinEPA-821-R-02-014,Section7.2.Thetestsalinityshallbedeterminedasfollows:(a)FortheAmericamysisbahiabioassays,theeffluentshallbeadjustedtoasalinityof20partsperthousand(ppt)withartificialseasalts.Thesalinityofthecontrol/dilutionwater(0%effluent)shallbe20ppt.Ifthesalinityoftheeffluentisgreaterthan20ppt,nosalinityadjustmentshallbemadetotheeffluentandthetestshallberunattheeffluentsalinity.Thesalinityofthecontrol/dilutionwatershallmatchthesalinityoftheeffluent.(b)FortheMenidiaberyllinabioassays,iftheeffluentsalinityislessthan5ppt,thesalinityshallbeadjustedto5pptwithartificialseasalts.Thesalinityofthecontrol/dilutionwater(0%effluent)shallbe5ppt.Ifthesalinityoftheeffluentisgreaterthan5ppt,nosalinityadjustmentshallbemadetotheeffluentandthetestshallberunattheeffluentsalinity.Thesalinityofthecontrol/dilutionwatershallmatchthesalinityoftheeffluent.(c)Ifthesalinityoftheeffluentrequiresadjustment,asalinityadjustmentcontrolshouldbepreparedandincludedwitheachbioassay.Thesalinityadjustmentcontrolisintendedtoidentifytoxicityresultingfromadjustingtheeffluentsalinitywithartificialseasalts.To preparethesalinityadjustmentcontrol,dilutethecontrol/dilutionwatertothesalinityoftheeffluentandadjustthesalinityofthesalinityadjustmentcontrolatthesametimeandtothesamesalinitythatthesalinityoftheeffluentisadjustedusingthesameartificialseasalts.e.QualityAssuranceRequirements(1)Astandardreferencetoxicant(SRT)qualityassurance(QA)chronictoxicitytestshallbeconductedwitheachspeciesusedintherequiredtoxicitytestseitherconcurrentlyorinitiatednomorethan30daysbeforethedateofeachroutineoradditionalfollow-uptestconducted.Additionally,theSRTtestmustbeconductedconcurrentlyifthetestorganismsareobtainedfromoutsidethetestlaboratoryunlessthetestorganismsupplierprovidescontrolchartdatafromatleastthelastfivemonthlychronictoxicitytestsusingthesamereferencetoxicantandtestconditions.IftheorganismsupplierprovidestherequiredSRTdata,theorganismsupplier'sSRTdataandthetestlaboratory'smonthlySRT-QAdatashallbeincludedinthereportsforeachcompanionroutineoradditionalfollow-uptestrequired.(2)Ifthemortalityinthecontrol(0%effluent)exceeds20%foreitherspeciesinanytestoranytestdoesnotmeet"testacceptabilitycriteria",thetestforthatspecies(includingthecontrol)shallbeinvalidatedandthetestrepeated.TestacceptabilitycriteriaforeachspeciesaredefinedinEPA-821-R-02-014,Section14.12(Americamysisbahia)andSection13.12(Menidiaberyllina).Therepeattestshallbeginwithin21daysafterthelastdayoftheinvalidtest.(3)If100%mortalityoccursinalleffluentconcentrationsforeitherspeciespriortotheendofanytestandthecontrolmortalityislessthan20%atthattime,thetest(includingthecontrol)forthatspeciesshallbeterminatedwiththeconclusionthatthetestfailsandconstitutesnon-compliance.(4)Routineandadditionalfollow-uptestsshallbeevaluatedforacceptabilitybasedontheobserveddoseresponserelationshipasrequiredbyEPA-821-R-02-014,Section10.2.6.,andtheevaluationshallbeincludedwiththebioassaylaboratoryreports.f.ReportingRequirements(1)ResultsfromallrequiredtestsshallbereportedontheDischargeMonitoringReport(DMR)asfollows:(a)RoutineandAdditionalFollow-upTestResults:ThecalculatedIC25foreachtestspeciesshallbeenteredontheDMR.(2)AbioassaylaboratoryreportforeachroutinetestshallbepreparedaccordingtoEPA-821-R-02-014,Section10,ReportPreparationandTestReview,andmailedtotheDepartmentattheaddressbelowwithin30daysafterthelastdayofthetest.(3)Foradditionalfollow-uptests,asinglebioassaylaboratoryreportshallbepreparedaccordingtoEPA821-R-02-014,Section10,andmailedwithin30daysafterthelastdayofthesecondvalidadditionalfollow-uptest.(4)Dataforinvalidtestsshallbeincludedinthebioassaylaboratoryreportfortherepeattest.(5)Thesamebioassaydatashallnotbereportedastheresultsofmorethanonetest.(6)Allbioassaylaboratoryreportsshallbesentto:6PERMITTEE:JEAPERMITNUMBER:FLOOO1031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkFloridaDepartmentofEnvironmentalProtectionNortheastDistrictOffice7825BaymeadowsWaySuiteB200Jacksonville,Florida32256g.TestFailuresEXPIRATIONDATE:(1)Atestfailswhenthetestresultsdonotmeetthelimitsin14.a.(l).(2)AdditionalFollow-upTests:(a)Ifaroutinetestdoesnotmeetthechronictoxicitylimitationin14.a.(l)above,thepermitteeshallnotifytheDepartmentattheaddressabovewithin21daysafterthelastdayofthefailedroutinetestandconducttwoadditionalfollow-uptestsoneachspeciesthatfailedthetestinaccordancewith14.d.(b)Thefirsttestshallbeinitiatedwithin28daysafterthelastdayofthefailedroutinetest.Theremainingadditionalfollow-uptestsshallbeconductedweeklythereafteruntilatotaloftwovalidadditionalfollow-uptestsarecompleted.(c)Theftrstadditionalfollow-uptestshallbeconductedusingacontrol(0%effluent)andaminimumoffivedilutions:100%,50%,25%,12.5%,and6.25%effluent.Thepermitteemaymodifythedilutionseriesinthesecondadditionalfollow-uptesttomoreaccuratelybracketthetoxicitysuchthatatleasttwodilutionsaboveandtwodilutionsbelowthetargetconcentrationandacontrol(0%effluent)arerun.AlltestresultsshallbeanalyzedaccordingtotheproceduresinEPA-821-R02-014.(3)Intheeventofthreevalidtestfailures(whetherroutineoradditionalfollow-uptests)withina12-monthperiod,thepermitteeshallnotifytheDepartment within21daysafterthelastdayofthethirdtestfailure.(a)Thepermitteeshallsubmitaplanforcorrectionoftheeffluenttoxicitywithin60daysafterthelastdayofthethirdtestfailure.(b)TheDepartmentshallreviewandapprovetheplanbefor.einitiation.(c)Theplanshallbeinitiatedwithin30daysfollowingtheDepartment'swrittenapprovaloftheplan.(d)ProgressreportsshallbesubmittedquarterlytotheDepartmentattheaddressabove.(e)Duringtheimplementationoftheplan,thepermitteeshallconductquarterlyroutinewholeeffluenttoxicitytestsinaccordancewith14.d.Additionalfollow-uptestsarenotrequiredwhiletheplanisinprogress.Followingcompletionorterminationoftheplan,thefrequencyofmonitoringforroutineandadditionalfollow-uptestsshallreturntothescheduleestablishedin14.b.(l).IfaroutinetestisinvalidaccordingtotheacceptancecriteriainEPA-821-R-02-014,arepeattestshallbeinitiatedwithin21daysafterthelastdayoftheinvalidroutinetest.(f)Uponcompletionoffourconsecutivequarterlyvalidroutineteststhatdemonstratecompliancewiththeeffluentlimitationin14.a.(l)above,thepermitteemaysubmitawrittenrequesttotheDepartmenttoterminatetheplan.TheplanshallbeterminateduponwrittenverificationbytheDepartmentthatthefacilityhaspassedatleastfourconsecutivequarterlyvalidroutinewholeeffluenttoxicitytests.Ifatestwithinthesequenceofthefourisdeemedinvalid,butisreplacedbyarepeatvalidtestinitiatedwithin21daysafterthelastdayofthe,invalidtest,theinvalidtestwillnotbecountedagainsttherequirementforfourconsecutivequarterlyvalidroutinetestsforthepurposeoftermi'natingtheplan.(4)Ifchronictoxicitytestresultsindicategreaterthan50%mortalitywithin96hoursinaneffluentconcentrationequaltoorlessthantheeffluentconcentrationspecifiedastheacutetoxicitylimitin14.(a)(2),theDepartmentmayrevisethispermittorequireacutedefinitivewholeeffluenttoxicitytesting.(5)Theadditionalfollow-uptestingandtheplandonotprecludetheDepartmenttakingenforcementactionforacuteorchronicwholeeffluenttoxicityfailures.[62-4.241,62-620.620(3)]15.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeLowVolumeWastesfromNGSEmergencyOverflowOutfallsD-010andD-Ollviaoverflowstructuresfromtheevaporation/percolationpondsandsettlingbasins,respectively,to7PERMITTEE:JEAPERMITNUMBER:FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:FL0001031-007(Major)MayS,2017SanCarlosCreek.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringReauirementsMonitoringMax/FrequencyofSampleSiteParameterUnitsMinLimitStatisticalBasisAnalysisTypeNumberFlowMGDMaxReportDailyMaximumDaily,whenEstimatedFLW-10dischargingFLW-11DurationofDischargehr/dayMaxReportDailyMaximumDaily,whenEstimatedEFF-10dischargingEFF-11Solids,TotalSuspendedmg/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11OilandGreasemg/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Arsenic,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Cadmium,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Chromium,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Iron,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Copper,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Lead,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Mercury,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Nickel,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11Zinc,TotalRecoverableug/LMaxReportDailyMaximumDaily,whenGrabEFF-10dischargingEFF-11pHMaxReportDailyMaximumDaily,whenGrabEFF-10s.u.dischargingEFF-1116.EffiuentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.A.15.andasdescribedbelow:MonitoringSiteNumberDescriptionofMonitoringSiteFLW-10FlowestimationoftheoverflowfromthepercolationpondstotheconcretespillwayanddischargeindirectlytoSanCarlosCreek.NotesFLW-11FlowestimationoftheoverflowfromtheriserpipeinthesouthsettlingbasinanddischargeindirectlytotheSanCarlosCreek.EFF-10OverflowfromthepercolationpondstotheconcretespillwayanddischargeindirectlytoSanCarlosCreek.EFF-11OverflowfromtheriserpipeinthesouthsettlingbasinanddischargeindirectlytotheSanCarlosCreek.17.EmergencyoverflowdischargesfromOutfallsD-010andD-011shallnotbeallowed,unlesscausedbyarainfalleventinexcessofthe25year,24hourrainfall(i.e.,8.7inches)ortheaccumulationofrainfallgreaterthanorequaltoavolumeof8.7inchestimesthesurfaceareaofthesouthsettlingpondorthepercolationpondfordischargefromD-010orD-011,respectively.DischargeshallbereportedtotheDepartmentimmediately.18.Forparametersotherthanflowandlengthofdischargeperiod,thehighestconcentrationofeachparametermonitoredshallbereportedontheDischargeMonitoringReport(DMR)asthedailymaximumconcentration.8PERMITTEE:JEAFACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FL0001031-007(Major)MayS,2017SamplesforallparametersshallbecollectedatthedischargefromtheoverflowweirfromtheevaporationIpercolationpondorsouthsettlingpondpriortoentryintothewetlandarea.19.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeSJRPPstormwaterfromOutfallD-002toBrownsCreek.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringReQuirementsMax/FrequencySampleMonitoringParameterUnitsMinLimitStatisticalBasisofAnalysisTypeSiteNumberFlowMODMaxReportDailyMaximumQuarterlyCalculatedEFF-2MaxReportMonthlyAverageSolids,TotalSuspendedmg/LMax50.0DailyMaximumQuarterlyGrabEFF-2Max50.0MonthlyAverageOilandGreasemg/LMax5.0DailyMaximumQuarterlyGrabEFF-2Max5.0MonthlyAveragepHMin6.5DailyMinimumQuarterlyGrabEFF-2s.u.Max8.5DailyMaximum20.EffiuentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.A19.andasdescribedbelow:MonitoringSiteNumberDescrit>tionofMonitoringSiteEFF-2Atthepointofdischargefromtherunoffsedimentationpondintoborrowpit.Notes21.ThelimitationsofConditionI.A19areapplicabletoanydischargeuptotheflowresultingfromarainfallequaltoorgreater7.44incheswhichisequivalenttothe10-year,24-hourrainfallevent.22.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeSJRPPCoalPileRunoffSedimentationPondDischargefromOutfallD-004toBrownsCreek.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringReauirementsMax/FrequencyofSampleMonitoringParameterUnitsMinLimitStatisticalBasisAnalvsisTvoeSiteNumberNotesFlowMODMaxReportDailyMaximumPerdischargeCalculatedFLW-4DurationofDischargeminMaxReportDailyMaximumPerdischargeCalculatedEFF-4Solids,TotalSuspendedmg/LMaxReportDailyMaximumPerdischargeGrabEFF-4Aluminum,TotalRecoverablemg/LMax1.5DailvMaximumPerdischargeGrabEFF-4Arsenic,TotalRecoverableug/LMax50DailyMaximumPerdischargeGrabEFF-4Chromium,TotalRecoverablemg/LMaxReportDailyMaximumPerdischargeGrabEFF-4Copper,TotalRecoverableug/LMax3.7DailyMaximumPerdischargeGrabEFF-4Iron,TotalRecoverablemg/LMax0.3DailyMaximumPerdischargeGrabEFF-4Lead,TotalRecoverableug/lMax8.5DailvMaximumPerdischargeGrabEFF-4Mercury,TotalRecoverableug/LMax0.025DailyMaximumPerdischargeGrabEFF-4Nickel,TotalRecoverableug/lMax8.3DailyMaximumPerdischargeGrabEFF-4Selenium,TotalRecoverableug/lMax71DailyMaximumPerdischargeGrabEFF-4Silver,TotalRecoverableug/LMaxReportDailyMaximumPerdischargeGrabEFF-4Zinc,TotalRecoverableug/LMax86DailyMaximumPerdischargeGrabEFF-49PERMmEE:

JEA FACILITY

: Northside Generating

Station

and

St. Johns

River Power

Park PERMIT NUMBER: EXPIRATION

DATE:

FLOOO 1031-007

(Major) MayS,

2017 pH

Effluent Limitations

Monitoring Requirements Max/

Frequency

of

Sample

Monitoring Parameter

Units

Min

Limit

Statistical

Basis

Analysis

Type

Site Number Min

6.5

Daily Minimum

Per discharge

Grab

EFF-4 s.u.

Max

8

. 5

Daily Maximum 23. Effiuent

samples

shall

be taken

at the monitoring

site locations

listed

in Permit Condition

I.A22

and

as described

below: Monitoring

Site Number

Description

of Monitoring

Site FLW-4

Calculated

flow

for Outfall

D-004. EFF-4

At the discharge

point

from

the coal

pile runoff sedimentation_ll_ond.

Notes 24. Discharge

to Browns

Creek

is not permitted

except

when

flow results

from

an event

equal

to

or greater

than

the 10-year,

24-hour

rainfall

event

(i.e.,

7.44 inches). 25. Discharge

of water

from

the Central Wastewater

Treatment

Facility

pump

sump

to the Coal

Pile Runoff Sedimentation

Pond

is permitted

during periods

when

the

pH

at Internal

Outfall

I -006

is not within permitted limitations,

provided

that available

excess detention

volume

is maintained

to accommodate

the

1 0 year,

24 hour rainfall

event

(i.e.,

7.44 inches). 26. During

the period beginning

on the issuance

date

and lasting through

the expiration

date

of this permit,

the permittee

is authorized

to discharge

SJRPP

Solid Waste Sedimentation

Pond Discharge

from Outfall

D-009 to Browns

Creek.

Such discharge

shall

be limited

and monitored

by

the permittee

as specified

below

and reported

in accordance

with Permit Condition

I.D.3.: Effluent Limitations

Monitoring Requirements Max/

Frequency

of

Sample

Monitoring Parameter

Units

Min

Limit

Statistical

Basis

Analysis

Type

Site Number Flow

MGD

Max

Report

Daily_ Maximum

Per discharge

Calculated

FLW-9 Duration

of Discharge

min

Max

Report

Daily Maximum

Per discharge

Meter

EFF-9 Solids, Settleable

mUL

Max

Report

Daily Maximum

Per discharge

Grab

EFF-9 Solids,

Total Dissolved

(TDS)

m_g[L

Max

Report

Daily Maximum

Per discharge

Grab

EFF-9 Solids,

Total Suspended

mg/L

Max

Report

Daily Maximum

Per discharge

Grab

EFF-9 Aluminum,

Total Recoverable

mwL

Max

1.5

Daily Maximum

Per discharge

Grab

EFF-9 Arsenic,

Total Recoverable

ug/L

Max

50

Daily Maximum

Per discharge

Grab

EFF-9 Chromium,

Total Recoverable

mg/L

Max

Report

Daily Maximum

Per discharge

Grab

EFF-9 Copper

Total Recoverable

ug/L

Max

3.7

Daily Maximum

Per discharge

Grab

EFF-9 Iron,

Total Recoverable

mg/L

Max

0.3

Daily Maximum

Per discharge

Grab

EFF-9 Lead

Total Recoverable

ug/L

Max

8.5

Daily Maximum

Per discharge

Grab

EFF-9 Mercury,

Total Recoverable

ug/L

Max

0.025

Daily Maximum

Per discharge

Grab

EFF-9 Nickel,

Total Recoverable

ug/L

Max

8.3

Daily Maximum

Per discharge

Grab

EFF-9 Selenium,

Total Recoverable

ug/L

Max

71

Daily Maximum

Per discharge

Grab

EFF-9 Silver,

Total Recoverable

ug/L

Max

Report

Daily Maximum

Per discharge

Grab

EFF-9 Zinc

Total Recoverable

ug/L

Max

86

Daily Maximum

Per dischar_ge

Grab

EFF-9 pH

Min

6.0

Daily Minimum

Per discharge

Grab

EFF-9 s

. u

.

Max

9

. 0

Daily Maximum 27. Effiuent

samples

shall

be taken

at the monitoring

site locations

listed

in Permit Condition

I.A.26.

and

as described

below:

10PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:MonitoringSiteNumberDescriptionSiteFLW-9Flowcalculationforthesolidwastesedimentationpondoverflow.EFF-9Atthesolidwastesedimentationpondoverflow.28.DischargetoBrownsCreekisnotpermittedexceptwhentheflowresultsfromaneventequaltoorgreaterthanthe10-year24-hourrainfallevent(7.44inches).29.Therunoffsedimentationpondshallbecapableofcontainingthe10-year,24-hourrainfallevent(7.44inches)fromtributaryareasplusallaccumulatedsilt.Quarterly,thepermitteeshallreporttheavailablesettlingpondvolume.ThisinformationshallbesubmittedalongwiththeDischargeMonitoringReport(DMR)form.ThepermitteemaybypasssedimentationpondrunoffanddischargedirectedtotheCWTFandsampleaccordingly.30.Thedischargeshallnotcontaincomponentsthatsettletoformputrescentdepositsorfloatasdebris,scum,oil,orothermatter.[62-302.500(1)(a)]B.InternalOutfalls1.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeSJRPPCoolingTowerBlowdownandCentralWastewaterTreatmentFacilityeffluentfromOutfall1-001totheNorthsideGeneratingStation'sencloseddischargebasin.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringRequirementsMax/FrequencyofSampleMonitoringParameterUnitsMinLimitStatisticalBasisAnalvsisTweSiteNumberNotesFlowMGDMaxReportDailyMaximumDaily;24hoursPumpFLW-2MaxReportMonthlyFLW-3Oxidants,TotalResidualmg/LMaxO.QlDailyMaximumWeeklyMultipleOUI-1SeeI.B.3Max0.01MonthlyAverageGrabandI.B.4TRO-DischargeTimemin/Max120DailyMaximumWeeklyMeterOUI-1SeeI.B.3dayMax120MonthlyAverageandI.B.4CyclesofConcentrationCyclesMax1.5DailyMaximumMonthlyCalculatedOUI-1SeeI.B.5SpecificConductanceurnhos/MaxReportDailyMaximumMonthly24-hrTPCOUI-1SeeI.B.6emReportMonthlyAverageTemperature,WaterDegFMax96.02DailyMaximumContinuousCalculatedOUI-1MaxMonthlyAveragepHMin6.5DailyMinimumMonthlyGrabOUI-1s.u.Max8.5DailyMaximumArsenic,TotalRecoverableug/LMaxReportDailyMaximumMonthly,whenGrabOUI-1Seei.B.7MaxReportMonthlyAveragedischargingMercury,TotalRecoverableug/LMaxReportDailyMaximumMonthly,whenGrabOUI-1SeeI.B.7MaxReportMonthlyASelenium,TotalRecoverableug/LMaxReportDailyMaximumMonthly,whenGrabOUI-1Seei.B.7MaxReportMonthlyAverageNitrogen,Ammonia,Totalmg/LMaxReportDailyMaximumWeekly,whenGrabOUI-1SeeI.B.7(asN)MaxReportMonthlyAINT-2Nitrogen,Kjeldahl,Totalmg/LMaxReportDailyMaximumWeekly,whenGrabOUI-1SeeI.B.7(asN)MaxReportMonthlyINT-22"DailyMaximum"shallbethehighestdailyaverage(mean)temperaturethroughoutagivencalendarmonth.Thedailymeantemperatureshallbecalculatedasthesumofalltemperaturemeasurementsduringagiven24hourday(12:00am-11:59pm)dividedbythenumberofmeasurementsduringthesameperiod.3"DailyAverage"(mean)shallbecalculatedasthesumofalltemperaturemeasurementsduringagiven24-hourperiod(12:00am-11:59pm)dividedbythenumberofmeasurementsduringthatsameperiod.11PERMITTEE:JEAPERMITNUMBER:FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:FL0001031-007(Major)MayS,2017EffluentLimitationsMonitoringRequirementsMax/FrequencyofSampleMonitoringParameterUnitsMinLimitStatisticalBasisAnalysisTypeSiteNumberNotesNitriteplusNitrate,TotalImg/LMaxReportDailyMaximumWeekly,whenGrabOUI-1SeeI.B.7det.(asN)MaxReportMonthlyAveragedischargingINT-2Nitrogen,Totalmg/LMaxReportDailyMaximumWeekly,whenCalculatedOUI-1SeeI.B.7MaxReportMonthlyAveragedischargingINT-2Nitrogen,TotalMonthly,whenOUI-1SeeI.B.7,(MonthlyNetLoading)lb/mthMaxReportMonthlyTotaldischargingCalculatedINT-2I.B.8andI.B.lONitrogen,TotalMonthly,whenOUI-1SeeI.B.7,(AnnualNetLoading)lb/yrMaxReportAnnualTotaldischargingCalculatedINT-2I.B.9,andI.B.lO2.EffluentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.B.l.andasdescribedbelow:MonitoringSiteNumberDescriptionofMonitoringSiteFLW-2TheflowmonitoringlocationofthefeedwaterwithdrawnfromtheNorthsidedischargefortheSt.JohnsRiverPowerParkcoolingtowers.FLW-3TheflowmonitoringlocationforthecombineddischargeofCentralWastewaterTreatmentFacilityeffluentandSt.JohnsRiverPowerParkcoolingtowerblowdownpriortocominglingwithNorthsideeffluent.OUI-1ThecombineddischargefromOutfalls1-005and1-006,atthemainplantdischargepriortoentryintotheNorthsideGeneratingStationdischargechannel.INT-2AttheintakestructureforcoolingtowersatSt.JohnsRiverPowerPark.3.NeitherFreeAvailableOxidants(FAO)norTotalResidualOxidants(TRO)shallbedischargedfromeithercoolingtowerformorethantwohoursperdayperunit.NotmorethanonecoolingtowershalldischargeFAOorTROatanyonetime.TROshallnotbedischargedduringperiodswhenTROisbeingdischargedfromanyunitattheNorthsideGeneratingStation.4.TotalResidualOxidants(TRO)meansthevalueobtainedusingtheamperometrictitrationmethodfortotalresidualchlorineortheHachmodel19300orequivalent).TestingforTRObytitrationshallbeconductedaccordingtoeitherthelow-levelamperometricmethod,ortheDPDcalorimetricmethodasspecifiedinsection4500-CIE.or4500CIG.,respectively,StandardMethodsfortheexaminationofWaterandWastewater,18thEdition(ormostcurrentedition).Thepermitteeshallcollectsamplesweeklywhenchlorineisinuse.TROmonitoringrequirementsforeitherUnit1or2arenotapplicableforanyweekinwhichchlorineisnotaddedtothatunit.Nomorethanoneunitshalldischargetotalresidualoxidantatanyonetime.MultiplegrabsforTROshallbedefinedasonceperfiveminutesduringTROdischargeperiodsof30minutesorlessandonceper15minutesforperiodsexceeding30minuteswithnolessthantwoanalysesduringtheperiodofTROdischarge(samplingshallbecontinueduntiltheendoftheTROdischarge).5.Cyclesofconcentrationshallbecalculatedbydividinga24-houraveragecoolingtowerblowdownTotalDissolvedSolids(TDS)valuefromthecombinedcoolingtowerdischargebya24-houraverageTDSvaluefromthecombinedcoolingtowerintake.TDSvaluesmaybeobtainedbycalibratedconductivitymeterreading.6.Thedailymaximumconductivityvalueshallbereportedasthemaximumconductivityvaluecorrespondingtothehighestnumberofcyclesofconcentrationsbetweenthecombinedcoolingtowerblowdowndischargefrom12PERMITTEE:JEAPERMITNUMBER:FLOOO1031-007(Major)MayS,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:Units1and2.Themonthlyaverageconductivityvalueshallbereportedastheaverageofallrecordedvaluesforthemonth.7.MonitoringforTotalRecoverableArsenic,Total RecoverableMercury,TotalRecoverableSelenium,TotalAmmonia,TKN,Nitrate+Nitrite,andTotalNitrogenisonlyrequiredwhentheSCRisinoperationandthefacilityisdischargingFGDblowdown.8.ThemonthlynetTotalNitrogen(TN)loadingisdefmedasthepoundsofTNdischargedatOUI-1minusthepoundsofTNwithdrawnatINT-2,overacorrespondingperiodoftime.ThefacilityshallreportthemonthlynetTNloadingwhichequalsthepoundsofTNdischargedduringamonthminusthepoundsTNwithdrawnduringthesamemonth.MonthlyTNwithdrawnanddischarged(inpoundspermonth)iscalculatedbasedontotalvolumeofwater/wastewaterwithdrawnanddischargedduringthatmonth.SamplesatINT-2andOUI-1shallbetakenconcurrently.IntakeanddischargeTNconcentrationsforanygivenmonthshallbetheaverageofallpairedTNsamplestakenduringthatmonth.Themonthlymassloadoftotalnitrogenshallbecalculatedasfollows:ML(Lbs/month)=Flow(MG/month)xTN(mg/L)x8.34(L-Lbs/MG-mg)Where:ML=Monthlymassloadoftotalnitrogen;(Lbs/month)Flow=Totalvolumeofeffiuentdischargedfromthepointsourceinagivenmonth;(milliongallons(MG))TN=MonthlyaverageconcentrationofTNcollectedatOUI-1andINT-2;(mg/L)9.TheannualnetTNloading(inpoundsperyear)onanygivenmonth isequaltothemonthlyTNnetloadingforthatmonthplusthepreviouselevenmonthlyTNloadingsandisconsideredarollingannualmaximumvalue.IfanannualTNloadislessthanzeroforamonthofreporting,thenthepermitteeshallreporttheannualloadas"0"ontheDischargeMonitoringReport(DMR)forthemonth.Theannualmassloadoftotalnitrogenshallbecalculatedasfollows:Theannualmassloadiscomputedusingarollingtwelve(12)monthperiod.Thecalculationshallbethesumofthetwelvemostrecentmonthlymassloadingsoftotalnitrogenstartingfromthesecondmonthfollowingpermitissuancemonth.10.ThepermitteeshallmeettheaggregatecapthroughcollectivelymanagingthetotalnitrogenloadsfromindividualJEAfacilities(ArlingtonEastWRF-FL0026441;BeaconHillsWWTF-FL0026778;BuckmanWWTF-FL0026000;DistrictIIWWTF-FL0026450;JacksonvilleHeightsWWTF-FL0023671;JulingtonCreekWWTF-FL0043591;MandarinWRF-FL0023663;SanPabloWWTF-FL0024767;SouthwestDistrictWWTF-FL0026468;WoodmereWWTF-FL0026786;andJEA-SJRPPFLOOO1031),whicharelistedintheJEA-AggregateTotalNitrogen(PermitNo.FL0620564).11.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeSJRPPUnits1and2CombinedCoolingTowerBlowdownfromInternalOutfall1-005totheMainPlantDischarge.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringRequirementsMax/FrequencyofSampleMonitoringParameterUnitsMinLimitStatisticalBasisAnalysisTypeSiteNumberNotesFlowMGDMaxReportDailyMaximumDaily;24hoursPumpLogsFLW-5MaxReportMonthlyAverage12.EffluentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.B.11.andasdescribedbelow:13PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:MonitoringSiteNumberDescriptionofMonitoringSiteFLW-5CalculatedaggregateblowdownflowofthetwocoolingtowersservingSJRPPUnits1and2.13.Continuouschlorinationofthecoolingtowermake-upsystemispermitted,providedthatcontinuouschlorinationdoesnotresultinadetectabledischargeofTROformorethantwohoursperday.14.Thepermitteeshall,withinthirtydaysofthepermitissuanceandyearlythereafter,providedcertificationthatthe126prioritypollutants(aslistedin40CFRPart423,AppendixA)arenotbeingdischargedindetectableconcentrationsinthecoolingtowerblowdownasaresultoftheadditionofanymaintenancechemicals.Complianceshallbedemonstratedbyoneofthethreemethods:Method1 :Samplingatafrequencyofnotlessthanonceperyearforallprioritypollutantsreferencedabovewithsubmissionofanalysisresultswitheachcertification.Method2:Submissionofcertification(s)fromthemanufacturerthateachproductusedcontainsnoprioritypollutants.Suchsubmissionisrequiredonlyonceforeachproductused,unlesssubsequentchangesintheproductformulationoccurortheproductisobtainedfromadifferentsource.Certificationsforallproductsinuseshallbemaintainedonsite.Method3:Calculationstoassurethatifprioritypollutantsarecontainedinanyproduct(s),nodischargeofanyindividualprioritypollutantcanoccuratconcentrationsgreaterthandetectable levelsusinganalyticalmethodsin40CFRPart136duetodilutionwithinthecoolingwatersystem.Thecertificationshallbeinthefollowingform:"Icertifythatnoprioritypollutantsatconcentrationsgreaterthandetectablelevelsusinganalyticalmethodsin40CFRPart136arebeingdischargedfromanymaintenancechemicalsaddedtothecoolingtowers.ComplianceisdemonstratedbyMethod__."15.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeSJRPPCentralWastewaterTreatmentFacilityWastewater(lowvolumewastes,metalcleaningwastewater,andotherindustrialwastewaterstreams)fromInternalOutfall1-006totheMainPlantDischargeCanal.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringRequirementsMonitoringMax/FrequencyofSampleSiteParameterUnitsMinLimitStatisticalBasisAnalysisTypeNumberNotesFlowMGDMaxReportDailyMaximumDaily;24hoursMeterFLW-6MaxReportMonthlyAveragemg/LMax30.0MonthlyAverageMonthly24-hrTPCOUI-6Seel.B.17Solids,TotalSuspendedMax50.0__-------------r-·-------------------------lb/dayMax1920.0DailyMaximumMonthlyCalculatedOUI-6Seei.B.17mg/LMax15.0MonthlyAverageMonthlyGrabOUI-6Seei.B.17OilandGreaseMaxr---20.0_------__c;;c__r---------------------r-----lb/dayMax260.0DailyMaximumMonthlyCalculatedOUI-6SeeI.B.l7pHMin6.0DailyMinimumContinuousRecorderOUI-6SeeI.B.l8s.u.Max9.0DailyMaximumLengthofLongestpHMinMax60DailyMaximumContinuousRecorderOUI-6Seel.B.l8ExcursionMax446MonthlyTotalCopper,TotalRecoverablemg/LMax1.0DailyMaximumMonthly24-hrTPCOUI-6Seel.B.l7Max1.0MonthlyAverageIron,TotalRecoverablemg/LMax1.0DailyMaximumMonthly24-hrTPCOUI-6Seel.B.l7Max1.0MonthlyAverage14PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:EffluentLimitationsMonitoringRequirementsMonitoringMax/FrequencyofSampleSiteParameterUnitsMinLimitStatisticalBasisAnalysisTypeNumberMercury,Totalug/LMaxReportDailyMaximumQuarterly,whenGrabOUI-6RecoverableMaxReportMonthlyAveragedischargingSilver,TotalRecoverableug/LMax0.0064DailyMaximumMonthly24-hrTPCOUI-6Max0.0064MonthlyAverageSelenium,Totalug/LMaxReportDailyMaximumMonthly,when24-hrTPCOUI-6RecoverableMaxReportMonthlyAveragedischargingPhosphorus,Total(asP)mg/LMax1.0DailyMaximumPerApplication24-hrTPCOUI-6MaxReportDailyAverageNitrogen,Kjeldahl,Totalmg/LMaxReportDailyMaximumMonthly,when24-hrTPCOUI-6(asN)MaxReportMonthlyAveragedischargingNitriteplusNitrate,Totalmg/LMaxReportDailyMaximumMonthly,when24-hrTPCOUI-6Idet.(asN)MaxReportMonthlyAveragedischargingNitrogen,Ammonia,Totalmg/LMaxReportDailyMaximumMonthly,when24-hrTPCOUI-6(asN)MaxReportMonthlyAveragedischargingNitrogen,Totalmg/LMaxReportDailyMaximumMonthly,when24-hrTPCOUI-6MaxReportMonthlyAveragedischargingNitrogen,Totallb/mthMaxReportMonthlyTotalMonthly,whenCalculatedOUI-6(MonthlyLoading)discharging16.EfiluentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.B.15.andasdescribedbelow:...MonitoringSiteNumberDescriptionofMonitoringSiteNotesSeeI.B.21SeeI.B.22SeeI.Bl9andI.B.20Seei.B.21SeeI.B.21SeeI.B.21SeeI.B.21SeeI.B.21FLW-6FlowmeasurementatdischargetotheCentralWastewaterTreatmentFacility(CWTF)priortomixingwithanyotherwastewaterstreams.·OUI-6AtdischargefromtheCWTFpriortomixingwithanyotherwastewaterstreams.17.DuringtheperiodswhenmetalcleaningwasteiscommingledwithlowvolumewasteandtreatedbytheCentralWastewaterTreatmentFacility(CWTF),TSS,Oil&Grease,TotalRecoverableCopper,andTotalRecoverableIronshallbemonitored.18.ThepermitteeshallmaintainthepHofsuchwastewaterwithintherangespecifiedinthispermit.Excursionsfromtherangearepermittedsubjecttothefollowinglimitations:a.ThetotaltimeduringwhichpHvaluesareoutsidetherequiredrangeofpHvaluesshallnotexceed7hoursand26minutesinacalendarmonth.b.NoindividualexcursionfromtherangeofpHvaluesshallexceed60minutes.c.ThepermitteeshallreporteachmonthforeachmonitoringstationwherepHismonitoredcontinuouslythefollowing:(1)thenumberofpHexcursions;(2)thedurationofeachexcursion;(3)thedateofeachexcursion;and(4)thetotaltimeofallexcursionscombined.d.AnexcursionisanunintentionalandtemporaryincidentinwhichthepHvalueofwastewaterexceedstherangespecifiedinthispermit.19.DuringtheperiodswhenmetalcleaningwastesarebeingtreatedbytheCWTF,TotalPhosphorousshallbemonitored.15PERMITTEE:JEAFACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FL0001031-007(Major)May8,201720.Themonitoringrequirementsforphosphorousareonlyapplicableifphosphate-containingchemicalsareusedinthemetalcleaningoperations.21.MonitoringforTotalRecoverableMercury,TotalAmmonia,TKN,Nitrate+Nitrite,andTotalNitrogenisonlyrequiredwhentheSCRisinoperationandthefacilityisdischargingFGDblowdown.22.MonitoringforTotalRecoverableSeleniumisonlyrequiredduringperiodswheneithermetalcleaningwasteiscommingledwithlowvolumewasteandtreatedbytheCWTForwhentheSCRisinoperationandthefacilityisdischargingFGDblowdowntotheCWTF.23.ThepermitteeshallplacethegravityfiltersinserviceorrecycletheCWTFeffiuenttothecoaipilerunoffsedimentationpondswhenclarifiereffluentturbidityisdeterminedtobegreaterthan10NTUbytheonlinemonitor.24.Thedischargesshallnotcontaincomponentsthatsettletoformputrescentdepositsorfloatasdebris,scum,oil,orothermatter.[62-302.500(1)(a)]C.LandApplicationSystems1.Duringtheperiodbeginningontheissuancedateandlastingthroughtheexpirationdateofthispermit,thepermitteeisauthorizedtodischargeindustrialwastewatertoNGSEvaporation/PercolationPondLandApplicationSystemR-001.SuchdischargeshallbelimitedandmonitoredbythepermitteeasspecifiedbelowandreportedinaccordancewithPermitConditionI.D.3.:EffluentLimitationsMonitoringRequirementsMonitoringMax/FrequencyofSampleSiteParameterUnitsMinLimitStatisticalBasisAnalysisTypeNumberNotesMaxReportAnnualAverageEFF-5Flow4MGDMaxReportDailyMaximumDaily;24hoursCalculated1PPI-1MaxReportMonthlyAverageMax8.5DailyMaximum5Days/WeekGrabEFF-56.5__pHs.u.------------MaxReportDailyMaximum5Days/WeekGrabPPI-1MinReportDailyMinimumSolids,TotalDissolved(TDS)mg/LMaxReportDailyMaximumMonthly24-hrEFF-5CompositePPI-1SpecificConductanceumhosMaxReportDailyMaximumMonthly24-hrEFF-5/emCompositePPI-1NitriteplusNitrate,TotalImg/LMaxReportDailyMaximumQuarterly24-hrEFF-5det.(asN)CompositePPI-1Lead,TotalRecoverableug/LMaxReportDailyMaximumMonthly24-hrEFF-5CompositePPI-1Nickel,TotalRecoverableug!LMaxReportDailyMaximumMonthly24-hrEFF-5CompositePPI-1Sodium,TotalRecoverablemg/LMaxReportDailyMaximumMonthly24-hrEFF-5CompositePPI-1Sulfate,Totalmg!LMaxReportDailyMaximumQuarterly24-hrEFF-5CompositePPI-1TurbidityNTUMaxReportDailyMaximumMonthly24-hrEFF-5CompositePPI-1Vanadium,TotalRecoverableug/LMaxReportDailyMaximumMonthly24-hrEFF-5CompositePPI-14Aowshallbecalculatedinconduitorthroughtreatmentplant.Theflowmetershallbecalibratedatleastannually.16-PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:2.EfiluentsamplesshallbetakenatthemonitoringsitelocationslistedinPermitConditionI.C.1.andasdescribedbelow:MonitoringSiteNumberDescriptionofMonitoringSiteEFF-5Effluentsamplingshallbefromwastewaterdischargetoevaporation/percolationpond.PPI-1WastewatersamplingshallbeattheinfluentdischargeintotheunlinedsettlingpondbeforepHisadjusted.D.OtherLimitationsandMonitoringandReportingRequirements1.Thesamplecollection,analyticaltestmethods,andmethoddetectionlimits(MDLs)applicabletothispermitshallbeconductedusingasufficientlysensitivemethodtoensurecompliancewithapplicablewaterqualitystandardsandeflluentlimitationsandshallbeinaccordancewithRule62-4.246,Chapters62-160and62-601,F.A.C.,and40CFR136,asappropriate.ThelistofDepartmentestablishedanalyticalmethods,andcorrespondingMDLs(methoddetectionlimits)andPQLs(practicalquantitationlimits),whichistitled"FAC62-4MDUPQLTable(April26,2006)"isavailableathttp://www.dep.state.fl.us/labs/library/index.htm.TheMDLsandPQLsasdescribedinthislistshallconstitutetheminimumacceptableMDUPQLvaluesandtheDepartmentshallnotacceptresultsforwhichthelaboratory'sMDLsorPQLsaregreaterthanthosedescribedaboveunlessalternateMDLsand/orPQLshavebeenspecificallyapprovedbytheDepartmentforthispermit.Anymethodincludedinthelistmaybeusedforreportingaslongasitmeetsthefollowing requirements:a.Thelaboratory'sreportedMDLandPQLvaluesfortheparticularmethodmustbeequalorlessthanthecorrespondingmethodvaluesspecifiedintheDepartment'sapprovedMDLandPQLlist;b.ThelaboratoryreportedMDLforthespecificparameterislessthanorequaltothepermitlimitortheapplicablewaterqualitycriteria,ifany,statedinChapter62-302,F.A.C.Parametersthatarelistedas"reportonly"inthepermitshallusemethodsthatprovideanMDL,whichisequaltoorlessthantheapplicablewaterqualitycriteriastatedin62-302,F.A.C.;andc.IftheMDLsforallmethodsavailableintheapprovedlistareabovethestatedpermitlimitorapplicablewaterqualitycriteriaforthatparameter,thenthemethodwiththeloweststatedMDLshallbeused.Whentheanalyticalresultsarebelowmethoddetectionorpracticalquantitationlimits,thepermitteeshallreporttheactuallaboratoryMDLand/orPQLvaluesfortheanalysesthatwereperformedfollowingtheinstructionsontheapplicabledischargemonitoringreport.Wherenecessary,thepermitteemayrequestapprovalofalternatemethodsorforalternativeMDLsorPQLsforanyapprovedanalyticalmethod.ApprovalofalternatelaboratoryMDLsorPQLsarenotnecessaryifthelaboratoryreportedMDLsandPQLsarelessthanorequaltothepermitlimitortheapplicablewaterqualitycriteria,ifany,statedinChapter62-302,F.A.C.Approvalofananalyticalmethodnotincludedintheabovereferencedlistisnotnecessaryiftheanalyticalmethodisapprovedinaccordancewith40CFR136ordeemedacceptablebytheDepartment.[62-4.246,62-160]2.Thepermitteeshallprovidesafeaccesspointsforobtainingrepresentativeinfluentandeflluentsampleswhicharerequiredbythispermit.[62-620.320(6)]3.Monitoringrequirementsunderthispermitareeffectiveonthefirstdayofthesecondmonthfollowingpermitissuance.Untilsuchtime,thepermitteeshallcontinuetomonitorandreportinaccordancewithpreviouslyeffectivepermitrequirements,ifany.Duringtheperiodofoperationauthorizedbythispermit,thepermitteeshallcompleteandsubmittotheDepartmentDischargeMonitoringReports(DMRs)inaccordancewiththefrequenciesspecifiedbytheREPORTtype(i.e.monthly,quarterly,semiannual,annual,etc.)indicatedontheDMRformsattachedtothispermit.MonitoringresultsforeachmonitoringperiodshallbesubmittedinaccordancewiththeassociatedDMRduedatesbelow.REPORTTypeonDMRMonitoringPeriodDueDateMonthlyfirstdayofmonth-lastdayofmonth28mdayoffollowingmonthQuarterlyJanuaryI -March31April28April1 -June30July2817PERMITTEE:FACILITY:JEANorthsideGeneratingStationandSt.JohnsRiverPowerParkJuly1 -September30October1-December31SemiannualJanuary1 -June30July1-December30AnnualJanuary1-December31PERMITNUMBER:EXPIRATIONDATE:October28January28July28January28January28FL0001031-007(Major)May8,2017DMRsshallbesubmittedforeachrequiredmonitoringperiodincludingmonthsofnodischarge.ThepermitteemaysubmiteitherpaperorelectronicDMRform(s).IfsubmittingpaperDMRform(s),thepermitteeshallmakecopiesoftheattachedDMRform(s).IfsubmittingelectronicDMRform(s),thepermitteeshalluseaDepartment-approvedelectronicDMRsystem.TheelectronicsubmissionofDMRformsshallacceptedonlyifapprovedinwritingbytheDepartment.Forpurposesofdeterminingcompliancewiththispermit,datasubmittedinelectronicformatislegallyequivalenttodatasubmittedonsignedandcertifiedDMRforms.ThepermitteeshallsubmitthecompletedDMRform(s)totheDepartmentbythetwenty-eighth(28th)ofthemonthfollowingthemonthofoperationattheaddressesspecifiedbelow:FloridaDepartmentofEnvironmentalProtectionWastewaterComplianceEvaluationSection,MailStation3551BobMartinezCenter2600BlairStoneRoadTallahassee,Florida32399-2400[62-620.610(18)]Unlessspecifiedotherwiseinthispermit,allreportsandotherinformationrequiredbythispermit,including24-hournotifications,shallbesubmittedtoorreportedto,asappropriate,theDepartment'sNortheastDistrictOfficeattheaddressspecifiedbelow:FloridaDepartmentofEnvironmentalProtectionNortheastDistrictOffice7825BaymeadowsWaySuiteB200Jacksonville,Florida32256PhoneNumber-(904)807-3300FAXNumber-(904)448-4366{AllFAXcopiesande-mailsshallbefollowedbyoriginalcopies.)[62-620.305]4.AllreportsandotherinformationshallbesignedinaccordancewiththerequirementsofRule62-620.305,F.A.C.[62-620.305]5.Ifthereisnodischargefromthefacilityonadaywhenthefacilitywouldnormallysample,thesampleshallbecollectedonthedayofthenextdischarge.[62-620.320(6)]6.Thedischargeofanywasteresultingfromthecombustionofchemicalmetalcleaningwastes,toxicwastes,orhazardouswastestoanywastestreamwhichultimatelydischargestowatersoftheUnitedStatesisprohibited,unlessspecificallyauthorizedelsewhereinthispermit.7.Thepermitteeshallnotstorecoal,soil,orothersimilarerodablematerialsinamannerinwhichrunoffisuncontrolled,norshallconstructionactivitiesbeconductedinamannerwhichproducesuncontrolledrunoffunlesssuchuncontrolledrunoffhasbeenspecificallyapprovedbytheDepartment."Uncontrolled"shallmeanwithoutsedimentationbasinorothercontrolsapprovedbytheDepartment.18PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:8.Thepermitteeshallmaintain,orobtain,recordsofrainfallrepresentativeoftheplantsiteconditionsatthefacility.Allperiodsofrainfall,whichexceedthe10-year,24-hourevent(7.44inches),shallbereportedtotheDepartmentasanattachmenttotheDMR.9.Thereshallbenodischargeofpolychlorinatedbiphenylcompoundssuchasthosecommonlyusedfortransformerfluid.[40CFRPart423.12(b)(2)]10.DischargeofanyproductregisteredundertheFederalInsecticide,Fungicide,andRodenticideActtoanywastestreamwhichultimatelymaybereleasedtowatersoftheStateisprohibitedunlessspecificallyauthorizedelsewhereinthispermit.Thisrequirementisnotapplicabletoproductsusedforlawnandagriculturalpurposesortotheuseofherbicidesifusedinaccordancewithlabeledinstructionsand anyapplicableStatepermit.ApermitrevisionfromtheDepartmentshallberequiredpriortotheuseofanybiocideorchemicaladditiveusedinthecoolingsystem(exceptchlorineasauthorizedelsewhereinthispermit)oranyotherportionofthetreatmentsystemwhichmaybetoxictoaquaticlife.Thepermitrevisionrequestshallinclude:a.Nameandgeneralcompositionofbiocideorchemicalb.Frequenciesofusec.Quantitiestobeusedd.Proposedeffluentconcentrationse.Acuteand/orchronictoxicitydata(laboratoryreportsshallbepreparedaccordingtoSection12ofEPAdocumentno.EPA-821-R-02-012EPentitled,MethodsforMeasuringtheAcuteToxicityofEffluentsandReceivingWatersforFreshwaterandMarineOrganisms,ormostcurrentaddition.)£Productdatasheetg.ProductlabelTheDepartmentshallreviewtheaboveinformationtodetermineifamajororminorpermitrevisionisnecessary.DischargeassociatedwiththeuseofsuchbiocideorchemicalisnotauthorizedwithoutapermitrevisionbytheDepartment.PermitrevisionsshallbeprocessedinaccordancewiththerequirementsofChapter62-620,F.A.C.11.Dischargeofanywasteresultingfromthecombustionoftoxic,hazardous,ormetalcleaningwastestoanywastestreamwhichultimatelydischargestowatersoftheStateisprohibited,unlessspecificallyauthorizedelsewhereinthispermit.12.Anywaterdrainedfromthefueloilstoragetanksorotherwater,whichmeetsthedefinitionof"PetroleumContactWater"asdefinedinRule62-740.030(1),F.A.C.,shallbedisposedofataDepartmentapprovedfacilityinaccordancewithChapter62-740,F.A.C.13.ThepermitteeisauthorizedtoutilizethefollowingwatertreatmentchemicalsandbiocidesattheSt.JohnsRiverPowerPark:ChemicalNameSystemUsedPurposeSodiumHypochloriteOn-siteReclaimedWaterStorageTanksatBio-growthControltheSt.JohnsPowerParksiteGaseousChlorineOn-siteReclaimedWaterStorageTanksatBio-growthControltheSt.JohnsPowerParksiteAS-55FGDAbsorberTanksAnti-foamingAgentDi-basicAcidFlueGasDesulfurizationSystemEnhanceSulfurDioxideRemoval14.Thepermitteeisauthorizedtouseanti-foamingagentAS-55attheSt.JohnsPowerParkfacilityintheFGDabsorbertanksatadosageratenottoexceed15mg/L(ppm).19PERMITTEE:JEAFACILITY:NorthsideGenerating StationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FL0001031-007(Major)May8,201715.ThepermitteeshallcontacttheDepartmentinaccordancewithConditionVl.8todevelopabiologicalPlanofStudy(POS)toevaluatetheeffectsofthefacility'sdischargeonthebalanced,indigenouspopulationofshellfish,fishandwildlifeinandonthereceivi.'lgbodyofwater.Theplanofstudyshallincludeanimplementationscheduleandmilestonesforgaugingprogresstowardcompletion.ThePOSshallbedesignedtogenerateinformationrelevanttothefollowingelements:1)apopulationtypicallycharacterizedbydiversityatalltrophiclevels;2)thecapacitytosustainitselfthroughcyclicseasonalchanges;3)presenceofnecessaryfoodchainspecies;4)non-dominationofpollution-tolerantspecies;and5)indigenous.ThepermitteeshallsubmitacopyofthePOStoeachofthefollowingagencies:AndFloridaDepartmentofEnvironmentalProtectionIndustrialWastewaterSection,MailStation3545BobMartinezCenter2600BlairStoneRoadTallahassee,Florida32399-2400U.S.EnvironmentalProtectionAgency,Region4MunicipalandIndustrialNPDESSectionPollutionControlandImplementationBranchWaterProtectionDivisionAtlantaFederalCenter61ForsythStreetAtlanta,Georgia30303-806016.Thepermitteeshallcontinuetheregularlyscheduledcleaninganddisposalofsolidsdepositedinthefollowingbasins:a.PrecipitationAreaSumpsforUnits1&2b.FGDAreaSumpsforUnits1&2c.CoalPileRunoffBasind.FGDPre-sedimentationBasin;ande.MetalCleaningWasteBasinsII.SLUDGEMANAGEMENTREQUIREMENTS1.DisposalofindustrialwastewatersludgeinasolidwastemanagementfacilitypermittedbytheDepartmentshallbeinaccordancewiththerequirementsofChapter62-701,F.A.C.Storage,transportation,anddisposalofsludge/solidscharacterizedashazardouswasteshallbeinaccordancewithrequirementsofChapter62-730,F.A.C.2.Thepermitteeshallkeeprecordsoftheamountofsludgedisposed,transported,orincineratedinwettons/day.Ifapersonotherthanthepermitteeisresponsibleforsludgetransporting,disposal,orincineration,thepermitteeshallalsokeepthefollowingrecords:a.Name,address,andtelephonenumberofanytransporter,and anymanifestsorbillofladingused;b.Nameandlocationofthesiteofdisposal,treatmentorincineration;c.Name,address,andtelephonenumberoftheentityresponsibleforthedisposal,treatment,orincinerationsite.III.GROUNDWATERREQUIREMENTS1.ThegroundwatermonitoringrequirementsfortheSt.JohnsRiverPowerParkareincorporatedintothefacility'sSiteCertification,LicenseNo.PA81-13.20

# PERMITTEE:

JEA 

# FACILITY:

Northside Generating

Station

and

St. Johns

River Power

Park PERMIT NUMBER: EXPIRATION

DATE:

FLOOO 1031-007

(Major) 

# MayS,

2017 2.

The ground

water monitoring requirements

within

Part

III

of this permit

apply

to 

# the JEA-Northside

Generating Station. 3.

The permittee

shall

give

at least 72-hours

notice

to the Department's

Northeast

District

Office,

prior

to 

# the installation

of any monitoring

wells. [62-520.600(6(h))J 4. Before construction

of new ground

water monitoring

wells,

a soil boring

shall

be made

at each monitoring

well location

to properly determine

the monitoring

well specification

such

as well depth,

screen interval,

screen

slot,

and filter pack. [62-520.600(6)(g)] 5. Within

30 days

after installation

of

a monitoring

well,

the permittee

shall submit

to the Department's

Northeast District

Office detailed information

on

the well's location

and construction

on DEP Form(s) 62-520.900(3),

Monitor Well Completion

Report. [62-532.410



# and 62-520.900(3)] 6.

All piezometers

and monitoring

wells

not part

of the approved

ground

water monitoring

plan

are

to be plugged

and abandoned

in accordance

with

Rule 62-532.500(4),

F.A.C.,

unless

future

use

is intended. [62-532.500(4)] 7.

For

the Land Application

System

R-001,

all ground

water quality

criteria specified



# in 62-520,

F.A.C.,

shall

be met

at the edge

of the zone

of discharge.

The zone

of discharge

for this existing

facility

shall extend horizontally

to the property

line

and vertically

to the base

of the surficial

aquifer. [62-520.200(26)]

[62-520.465] 8.

The ground

water minimum

criteria specified

in Rule 62-520.400,

F.A.C.,

shall

be met within

the zone

of discharge. [62-520.400

and 62-520.420(4)] 9.

If the concentration

for

any constituent

listed

in Permit Condition

III.12.



# in the natural background

quality

of the ground

water

is greater

than

the stated maximum,

or



# in the case

of pH

is also

less than

the minimum,

the representative

background

quality

shall

be

the prevailing

standard. [62-520.420(2)] 1 

# 0. During

the period

of operation authorized

by this permit,

the permittee

shall continue

to sample

and analyze

ground water

at the existing monitoring

wells identified



# in Permit Condition

III.11,

below,



# in accordance

with

this permit and

the approved

ground

water monitoring

plan prepared

in accordance

with

Rule 62-520.600,

F.A.C. [62-520.600] 11.

The following monitoring

wells

shall

be sampled

for Land Application

System

R-001.: Monitoring

Alternate

Well Name

and/or Description

of

Latitude

Longitude

Depth

Aquifer

New

or Well

ID

Monitoring

Location

0



# '

"

0



# '



# "

(Feet) Monitored

Existing MWI-16

NS-16:

East

of Coal

Pile

and

Pet Coke

30

25 14.4622

81

33 18.9473

16 Surficial

Existing Storage

Areas MWB-19

NS-19:

1000'

NW ofPerc

Pond

C

30

25 21.3589

81

33 16.2379



# 10 Surficial

Existing MWC-22

NS-22:

70'

SE

of Perc Pond

B

30

25 18.3835

81

33 01.6740

10 Surficial

Existing MWI-23

NS-23:

30'

SE

of Perc Pond

B

30

25 18.4005

81

33 00.7732

15 Surficial

Existing MWC-27

NS-27:

SE

of Coal

Pile

and

Pet Coke Storage

30

25 08.1925

81

33 18.4907

16 Surficial

Existing Areas. MWI-28

NS-28:

300'

SW ofNS-23

30

25 17.8683

81

33 03.7869

15 Surficial

Existing MWI-29

NS-29:

50'

SW

of south sludge

bed

30

25 14.3421

81

33 10.0583



# 13 Surficial

Existing MWI-30

NS-30:

SE comer

of Lime Settling

Ponds.

30

25 15.0458

81

33 00.0249

15 Surficial

Existing MWC-32

AW-FS:

SW ofEZBase

Production

Facility.

30

25 17.6767

81

33 36.2274

22

Surficial

Existing MWC-33

AW-JS:

South ofEZBase

Production

Facility.

30

25 13.6999

81

33 29.1248

22

Surficial

Existing MWC

= Compliance;

MWB

- Background;

MWI

= lntennedtate;

MWP =Ptezometer 

# [62-520.600]

21PERMITTEE:JEAFACILITY:NorthsideGenerating StationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FL0001031-007(Major)May8,201712.ThefollowingparametersshallbeanalyzedforeachmonitoringwellidentifiedinPermitCondition111.10.:ParameterComplianceWellUnitsSampleTypeMonitoringLimitFrequencyWaterLevelRelativetoNGVDReportftInSituQuarterlySpecificConductanceReportumhos/cmInSituQuarterlypHReports.u.InSituQuarterlySolids,TotalDissolvedReportmg/LGrabQuarterlyLead,TotalRecoverable15uJtiLGrabQuarterlyNickel,TotalRecoverable100ug/LGrabQuarterlyNitriteplusNitrate,Total1det.(asN)10mg/LGrabQuarterlySodium,TotalRecoverable*mg/LGrabQuarterlyVanadium,TotalRecoverable**ug/LGrabQuarterlyTurbidityReportNTUGrabQuarterlyChlorideReportmg/LGrabQuarterlySulfateReportmJtiLGrabQuarterlyMWC-Compliance;MWB=Background;MWI=Intenned1ate;MWP-Piezometer22PERMITTEE:JEAFACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FL0001031-007(Major)May8,2017*AsodiumexemptionforthisfacilitywasgrantedonJanuary5,2010,andthecompliancewelllimitisreportonly.Thisexemptionexpiresinconjunctionwiththispermit,andthefacilitymustreapplypriortotheexpirationdateofthispermit.**VanadiumcurrentlyhasaGuidanceConcentrationof49ug!L.[62-520.600(11)(b)]13.Within60daysafterpermitissuance,thePermitteeshallconductanexpandedsamplingofmonitoringwellMWI-23andMWC-32,fortheprimaryandsecondarydrinkingwaterparametersincludedinChapter62-550,Tables1,4,and6,(excludingasbestos),plusturbidityandvanadium.AllanalyticalresultsfromthisexpandedsamplingshallbesubmittedtotheDepartmentwithin60daysfollowingthesampleevent.[62-520.600(5)(a)(2)]14.Between6to12monthsprecedingpermitexpiration,thepermitteeshallconductanexpandedsamplingofmonitoringwellMWI-23andMWC-32,fortheprimaryandsecondarydrinkingwaterparameterslistedinChapter62-550,Tables1,4and6,(excludingasbestos),plusturbidityandvanadium.Allanalyticalresultsfromthisexpandedsamplingshallbesubmittedasanattachmenttothepermitrenewalapplication.[62-520.600(5)(b)]15.ThisfacilityisanexistinginstallationasdefinedinRule62-520,F.A.C,andisexemptfromcompliancewithsecondarystandardsforgroundwaterattheedgeofthezoneofdischargeinaccordancewithRules62-520.520,and62-522.300(8),F.A.C.16.Waterlevelsshallberecordedbeforeevacuatingeachwellforsamplecollection.Elevationreferencesshallincludethetopofthewellcasingandlandsurfaceateachwellsite(NAVDallowable)ataprecisionofplusorminus0.01foot.[62-520.600(11)(c)]17.Groundwatermonitoringwellsshallbepurgedpriortosamplingtoobtainrepresentativesamples.[62-160.21OJ18.Analysesshallbeconductedonunfilteredsamples,unlessfilteredsampleshavebeenapprovedbytheDepartment'sNortheastDistrictOfficeasbeingmorerepresentativeofgroundwaterconditions.[62-520.310(5)]19.Ifanymonitoringwellbecomesdamagedorinoperable,thepermitteeshallnotifytheDepartment'sNortheastDistrictOfficeimmediatelyandadetailedwrittenreportshallfollowwithinsevendays.Thewrittenreportshalldetailwhatproblemhasoccurredandremedialmeasuresthathavebeentakentopreventrecurrence.AllmonitoringwelldesignandreplacementshallbeapprovedbytheDepartment'sNortheastDistrictOfficepriortoinstallation.[62-520.600][62-620.320(6)]20.GroundwatermonitoringtestresultsshallbesubmittedonPartDofDEPForm62-620.910(10),orsuchotherformatasapprovedbytheDepartment,accordingtothefollowingschedule,andtotheaddressspecifiedinPermitConditionI.D.3.:SAMPLEPERIODQuarterlyREPORTDEADLINE(January-March)XApril28th(April-June)XJuly28m(July-September)XOctober281n(October-December)XJanuary28th[62-520.600(11)(b)JIV.ADDITIONALLANDAPPLICATIONREQUIREMENTSSectionIVisnotapplicabletothisfacility.23PERMITTEE:JEAFACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkPERMITNUMBER:EXPIRATIONDATE:FL0001031-007(Major)May8,2017V.OPERATIONANDMAINTENANCEREQUIREMENTS1.Duringtheperiodofoperationauthorizedbythispermit,thewastewaterfacilitiesshallbeoperatedunderthesupervisionofapersonwhoisqualifiedbyformaltrainingand/orpracticalexperienceinthefieldofwaterpollutioncontrol.[62-620.320(6)]2.Thepermitteeshallmaintainthefollowingrecordsandmakethemavailableforinspectiononthesiteofthepermittedfacility.a.Recordsofallcompliancemonitoringinformation,includingallcalibrationandmaintenancerecordsandalloriginalstripchartrecordingsforcontinuousmonitoringinstrumentation,including,ifapplicable,acopyofthelaboratorycertificationshowingthecertificationnumberofthelaboratory,foratleastthreeyearsfromthedatethesampleormeasurementwastaken;b.Copiesofallreportsrequiredbythepermitforatleastthreeyearsfromthedatethereportwasprepared;c.Recordsofalldata,includingreportsanddocuments,usedtocompletetheapplicationforthepermitforatleastthreeyearsfromthedatetheapplicationwasfiled;d.Acopyofthecurrentpermit;e.Acopyofanyrequiredrecorddrawings;andf.Copiesofthelogsandschedulesshowingplantoperationsandequipmentmaintenanceforthreeyearsfromthedateofthelogsorschedules.[62-620.350]VI.SCHEDULES1.Thefollowingimprovementactionsshallbecompletedaccordingtothefollowingschedule.TheStormwaterPollutionPreventionPlan(SWPPP)forNGSshallbepreparedandimplementedinaccordancewithPartVIIofthispermit.Ilml!rovementActionIComl!letionDateI1.DevelopandimplementSWPPP6monthsfrompermitissuance.2.CompletePlanSummary2yearsfrompermitissuance.3.Progress/UpdateReport3years,andthenannualthereafter.[62-620.320(6)]2.Ifthepermitteewishestocontinueoperationofthiswastewaterfacilityaftertheexpirationdateofthispermit,thepermitteeshallsubmitanapplicationforrenewalnolaterthanone-hundredandeightydays{180)priortotheexpirationdateofthispermit.ApplicationshallbemadeusingtheappropriateformslistedinRule62-620.910,F.A.C.,includingsubmittaloftheappropriateprocessingfeesetforthinRule62-4.050,F.A.C.[62-620.335(1)and(2)]3.Within12monthsoftheeffectivedateofthispermit,thepermitteeshallscheduleameetingwiththeDepartmenttodiscussthecontentsoftheaquaticorganismreturnplaninaccordancewithConditionI.A.13andshallsubmittheplantotheDepartmentwithin18monthsoftheeffectivedateofthispermit.Theplanshallbeimplementedwithin30monthssubsequenttoapprovalbytheDepartment.4.Withinsixmonthsoftheeffectivedateofthispermit,thepermitteeshallscheduleameetingwiththeDepartmenttodiscussthecontentsofthebiologicalplanofstudy(POS)inaccordancewithConditionI.A.15andshallsubmittheplantotheDepartmentwithin12monthsoftheeffectivedateofthispermit.Theplanshallbeimplementedwithin24monthssubsequenttotheapprovalbytheDepartmentandtheresultsshallbesubmittedwiththepermitrenewalapplication.24PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)MayS,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:5.ThepermitteeshallcomplywiththeimplementationscheduleofEPA'sSteamElectricPowerGenerationPointSourceeffluentguidelinesuponfinalpromogationoftherevisedfederalguidelines.VII.STORMWATERPOLLUTIONPREVENTIONPLANS1.GeneralRequirementsInaccordancewithSection304(e)and402(a)and(b)oftheCleanWaterAct(CWA)asamended,33U.S.C.§§1251etseq.,andthePollutionPreventionActof1990,42U.S.C.§§13101-13109,thepermitteemustdevelopandimplementaplanforutilizingpracticesincorporatingpollutionpreventionmeasures.Referencestobeconsideredindevelopingtheplanare"CriteriaandStandardsforBestManagementPracticesAuthorizedUnderSection304(e)oftheAct,"foundat40CFR122.44SubpartKandtheStormWaterManagementIndustrialActivitiesGuidanceManual,EPN833-R92-002andotherEPAdocumentsrelatingtoBestManagementPracticeguidance.a.Definitions(1)Theterm"pollutants"referstoconventional,non-conventionalandtoxicpollutants.(2)Conventionalpollutantsare:biochemicaloxygendemand(BOD),suspendedsolids,pH,fecalcoliformbacteriaandoil&grease.(3)Non-conventionalpollutantsarethosewhicharenotdefinedasconventionalortoxic.(4)Toxicpollutantsinclude,butarenotlimitedto:(a)anytoxicsubstancelistedinSection307(a)(1)oftheCWA,anyhazardoussubstancelistedinSection311oftheCWA,orchemicallistedinSection313(c)oftheSuperfundAmendmentsandReauthorizationActof1986;and(b)anysubstance(thatisnotalsoaconventionalornon-conventionalpollutantexceptammonia)forwhichEPAhaspublishedanacuteorchronictoxicitycriterion.(5)"SignificantMaterials"isdefinedasrawmaterials;fuels;materialssuchassolventsanddetergents;hazardoussubstancesdesignatedunderSection101(14)ofCERCLA;and anychemicalthefacilityisrequiredtoreportpursuanttoEPCRA,Section313;fertilizers;pesticides;andwasteproductssuchasashes,slagandsludge.(6)"Pollutionprevention"and"wasteminimization"refertothefirsttwocategoriesofEPA'spreferredhazardouswastemanagementstrategy:first,sourcereductionandthen,recycling.(7)"Recycle/Reuse"isdefinedastheminimizationofwastegenerationbyrecoveringandreprocessingusableproductsthatmightotherwisebecomewaste;orthereuseorreprocessingofusablewasteproductsinplaceoftheoriginalstock,orforotherpurposessuchasmaterialrecovery,materialregenerationorenergyproduction.(8)"Sourcereduction"meansanypracticewhich:(a)reducestheamountofanypollutantenteringawastestreamorotherwisereleasedintotheenvironment(includingfugitiveemissions)priortorecycling,treatmentordisposal;and(b)reducesthehazardstopublichealthandtheenvironmentassociatedwiththereleaseofsuchpollutant.Thetermincludesequipmentortechnologymodifications,processorproceduremodifications,reformulationorredesignofproducts,substitutionofrawmaterials,andimprovementsinhousekeeping,maintenance,training,orinventorycontrol.Itdoesnotincludeanypracticewhichaltersthephysical,chemical,orbiologicalcharacteristicsorthevolumeofapollutantthroughaprocessoractivitywhichitselfisnotintegralto,orpreviouslyconsiderednecessaryfor,theproductionofaproductortheprovidingofaservice.(9)"SWPPP"meansaStormWaterPollutionPreventionPlanincorporatingtherequirementsof40CFR§125,SubpartK,pluspollutionpreventiontechniques,exceptwhereotherexistingprogramsaredeemedequivalentbythepermittee.Thepermitteeshallcertifytheequivalencyoftheotherreferencedprograms.(lO)Theterm"material"referstochemicalsorchemicalproductsusedinanyplantoperation(i.e.,causticsoda,hydrazine,degreasingagents,paintsolvents,etc.).Itdoesnotincludelumber,boxes,packingmaterials,etc.(11)Theterm"allowablenon-stormwaterdischarges"referstothefollowingdischargesthatmaybedischargedthroughstormwateroutfallsunlessidentifiedbytheDepartmentassourcesofpollutants:•Dischargesfromfire-fightingactivities;•Firehydrantflushings;•Potablewater,includingwaterlineflushings;•Uncontaminatedcondensatefromairconditioners,coolers,andothercompressorsandfromtheoutsidestorageofrefrigeratedgasesorliquids;25

# PERMITTEE: FACILITY:

JEA Northside Generating

Station

and

St. Johns

River Power

Park • Irrigation

drainage;

PERMIT NUMBER: EXPIRATION

DATE: FL0001031-007

(Major) May

8, 2017 • Landscape

watering

provided

all pesticides,

herbicides

and fertilizer

have

been applied

in accordance with

the approved

labeling; • Pavement

wash waters

where

no detergents

are used

and

no spills

or leaks

of toxic

or hazardous materials

have occurred

(unless

all spilled material



# has been removed); • Routine

external

building washdown

that does

not

use detergents; • Uncontaminated

ground

water

or spring

water; • Foundation

or footing



# drains

where

flows

are

not contaminated

with process materials;

and • Incidental wind-blown

mist

from cooling

towers

that collects

on rooftops

or adjacent

portions

of your facility,

but

not intentional

discharges

from

the coolin

g tower

(e.g. "piped"

cooling

tower blowdown

or drains). 2. Storm

Water Pollution Prevention

Plan The permittee

shall develop

and implement

a SWPPP

for

the facility,

which

is the source

of wastewater

and storm water discharges,

covered

by this permit.

The plan

shall

be directed

toward reducing

those pollutants

of concern which discharge

to surface

waters

and shall

be prepared

in accordance

with

good engineering

and good housekeeping

practices.

For

the purposes

of this permit, pollutants

of concern

shall

be limited

to 

# toxic pollutants,

as defined

above,

known

to the discharger.

The plan

shall address



# all activities

which

could

or

do contribute

these pollutants

to the surface

water discharge,

including

process, treatment,

and ancillary activities. a. Signatory

Authority

& Management Responsibilities The SWPPP

shall

be signed

by permittee

or their

duly authorized representative

in accordance

with

rule

62- 620.305(2)(a)

and

(b).

The SWPPP

shall

be reviewed

by plant environmental/engineering

staff

and plant manager.

Where required

by Chapter 471-(P.E.)

or Chapter

492 (P.G.) Florida Statutes, applicable

portions

of the SWPPP

shall

be signed

and sealed

by the professional(s)

who prepared

them. A copy

of the plan

shall

be retained

at the facility

and shall

be made available

to the permit

issuing authority upon request. The SWPPP

shall contain

a written statement

from corporate

or plant management

indicating management's commitment

to the goals

of the BMP program.

Such statements

shall

be publicized

or made known

to

all facility employees. Management

shall

also provide

training

for

the individuals

responsible

for implementing the SWPPP. b. SWPPP Requirements (1)

A topographic

map extending one-quarter

mile beyond

the property boundaries

of the facility, showing:

the facility,

surface

water bodies,

wells (including

injection

wells), seepage

pits, infiltration

ponds,

and

the discharge

points

where

the facility's

storm

water discharges

to

a municipal

storm

drain system

or other water

body.

The requirements

of this paragraph

may

be included

on

the

site map

if appropriate. (2)

A site map showing: (a)

The storm

water conveyance

and discharge

structures; (b)

An outline

of the storm

water drainage

areas

for each storm

water discharge

point; (c) Paved

areas

and buildings; (d) Areas

used

for outdoor manufacturing,

storage,

or disposal

of significant

materials,

including

activities that generate significant

quantities

of dust

or particulates; (e) Location

of existing

or future

storm

water structural

control measures/practices

(dikes, coverings, detention

facilities,

etc.); (f) Surface

water locations

and/or municipal

storm

drain locations; (g) Areas

of existing

and potential

soil erosion; (h) Vehicle

service

areas;

and (i) Material

loading, unloading,

and access



# areas. (3) Anarrative

description

of the following: (a)

The nature

of the industrial

activities conducted

at the site, including

a description

of significant materials

that

are treated,

stored

or disposed

of

in

a manner

to allow exposure

to storm

water; (b) Materials, equipment,

and vehicle management

practices employed

to minimize

contact

of significant materials

with storm

water discharges;

26PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:(c)Existingorfuturestructuralandnon-structuralcontrolmeasures/practicestoreducepollutantsinstormwaterdischarges;(d)Industrialstormwaterdischargetreatmentfacilities;(e)Methodsofonsitestorageanddisposalofsignificantmaterials;(f)Overallobjectives(bothshort-termandlong-term)andscopeoftheplan,specificreductiongoalsforpollutants,anticipateddatesofachievementofreduction,andadescriptionofmeansforachievingeachreductiongoal;(g)Adescriptionofproceduresrelativetospillprevention,control&countermeasuresandadescriptionofmeasuresemployedtopreventstormwatercontamination;(h)Adescriptionofpracticesinvolvingpreventivemaintenance,housekeeping,recordkeeping,inspections,andplantsecurity;and(i)Thedescriptionofawasteminimizationassessmentperformedinaccordancewiththeconditionsoutlinedinconditioncbelow,resultsoftheassessment,andascheduleforimplementationofspecificwastereductionpractices.(4)Alistofthetypesofpollutantsthathaveareasonablepotentialtobepresentinstormwaterdischargesinsignificantquantities.(5)Anestimateofthesizeofthefacilityinacresorsquarefeet,andthepercentofthefacilitythathasimperviousareassuchaspavementorbuildings.(6)Asummaryofexistingsamplingdatadescribingpollutantsinstormwaterdischarges.c.WasteMinimizationAssessmentThepermitteeisrequiredtoconductawasteminimizationassessment(WMA)forthisfacilitytodetermineactionsthatcouldbetakentoreducewasteloadingandchemicallossestoallwastewaterand/orstormwaterstreams.d.PollutionPreventionCommittee:Apollutionpreventioncommitteewithinth.eplantorganizationshallbeappointed.ThesemembersshallberesponsiblefordevelopingtheSWPPPandassistingtheplan.tma..11agerinitsimplementation,maintenance,andrevision.e.EmployeeTraining(1)Thepermitteeshalldescribethestormwateremployeetrainingprogramforthefacility.Thedescriptionshallincludethetopicstobecovered,suchasspillresponse,goodhousekeepingandmaterialmanagementpractices,andshallidentifyperiodicdates(e.g.,every6monthsduringthemonthsofJulyandJanuary)forsuchtraining.Thepermitteeshallprovideemployeetrainingforallemployeesandcontractorsthatworkinareaswhere industrialmaterialsoractivitiesareexposedtostormwater,andforemployeesthatareresponsibleforimplementingactivitiesidentifiedintheSWPPP(e.g.,inspectors,maintenancepeople).TheemployeetrainingshallinformfacilitypersonnelandcontractorsofthecomponentsandgoalsofthefacilitySWPPP.(2)Eachemployeeandcontractorthatworksinanareaswhereindustrialmaterialsoractivitiesareexposedtostormwater,andeachemployeethatisresponsibleforimplementing activitiesidentifiedintheSWPPPshallundergotrainingatleastonceayear.Trainingrecordsshallincludetrainee'sname,signature,dateoftrainingandtopicscovered.Recordsshallberetainedon-siteforaminimumofthreeyearsf.PlanDevelopment&Implementation(1)TheSWPPPshallbedevelopedandimplemented6monthsaftertheeffectivedateofthispermit,unlessanylaterdatesarespecifiedinthispermit.AnyportionoftheSWPPPwhichisongoingatthetimeofdevelopmentorimplementationshallbedescribedintheplan.Anywastereductionpracticewhichisrecommendedforimplementationoveraperiodoftimeshallbeidentifiedintheplan,includingascheduleforitsimplementation.(2)AtleastonceayearthepersonnelnamedintheSWPPPshallverifythatthedescriptionofpotentialpollutantsourcesrequiredunderthispermitisaccurate;thesitemapasrequiredintheSWPPPhasbeenupdatedorotherwisemodifiedtoreflectcurrentconditions;andthecontrolstoreducepollutantsinstormwaterdischargesassociatedwithindustrialactivityidentifiedintheSWPPParebeingimplementedandareadequate.g.SubmissionofPlanSummary&Progress/UpdateReports27PERMITTEE:JEAPERMITNUMBER:FLOOO1031-007(Major)MayS,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:(1)PlanSummary:Notlaterthan2yearsaftertheeffectivedateofthepermit,asummaryoftheSWPPPshallbedevelopedandmaintainedatthefacilityandmadeavailabletothepermitissuingauthorityuponrequest.Thesummaryshouldincludethefollowing:abriefdescriptionofthepian;itsimplementationprocess,schedulesforimplementingidentifiedwastereductionpractices,andalistofallwastereductionpracticesbeingemployedatthefacility.TheresultsofwasteminimizationassessmentstudiesalreadycompletedaswellasanyscheduledorongoingWMAstudiesshallbediscussed.(2)Progress/UpdateReports:Annuallythereafterforthedurationofthepermitprogress/updatereportsdocumentingimplementationoftheplanshallbemaintainedatthefacilityandmadeavailabletothepermitissuingauthorityuponrequest.Thereportsshalldiscusswhetherornotimplementationschedulesweremetandreviseanyschedules,asnecessary.Theplanshallalsobeupdatedasnecessaryandtheattainmentorprogressmadetowardspecificpollutantreductiontargets documented.ResultsofanyongoingWMAstudiesaswellasanyadditionalschedulesforimplementationofwastereductionpracticesshallbeincluded.(3)Atimetableforthevariousplanrequirementsfollows:TimetableforSWPPPRequirements:REQUIREMENTTIMEFROMEFFECTIVEDATEOFTHISPERMITCompleteSWPPPCompletePlanSummaryProgress/UpdateReports6months2years3years,andthenannuallythereafterThepermitteeshallmaintaintheplanandsubsequentreportsatthefacilityandshallmaketheplanavailabletotheDepartmentuponrequest.h.PlanReview&ModificationIftheSWPPPisdeterminedtobeinsufficientfollowingreviewbytheDepartment,thepermitteewillbenotifiedthattheSWPPPdoesnotmeetoneormoreoftheminimumrequirementsofthisPart.UponsuchnotificationfromtheDepartment,thepermitteeshallamendtheplanandshallsubmittotheDepartmentawrittencertificationthattherequestedchangeshavebeenmade.UnlessotherwiseprovidedbytheDepartment,thepermitteeshallhave30daysaftersuchnotificationtomakethechangesnecessary.ThepermitteeshallmodifytheSWPPPwheneverthereisachangeindesign,construction,operation,ormaintenance,whichhasasignificanteffectonthepotentialforthedischargeofpollutantstowatersoftheStateoriftheplanprovestobeineffectiveinachievingthegeneralobjectivesofreducingpollutantsinwastewaterorstormwaterdischarges.ModificationstotheplanmaybereviewedbytheDepartmentinthesamemannerasdescribedabove.Thepermitteemayincorporateapplicableportionsofplanspreparedforotherpurposes.PlansorportionsofplansincorporatedintoaSWPPPbecomeenforceablerequirementsofthispermit.VDI.OTHERSPECIFICCONDITIONSA.SpecificConditionsApplicabletoAllPermits1.WhererequiredbyChapter471orChapter492,F.S.,applicableportionsofreportsthatmustbesubmittedunderthispermitshallbesignedandsealedbyaprofessionalengineeroraprofessionalgeologist,asappropriate.[62-620.310(4)]2.Drawings,plans,documentsorspecificationssubmittedbythepermittee,notattachedhereto,butretainedonfileattheDepartment'sNortheastDistrictOffice,aremadeaparthereof.3.ThispermitsatisfiesIndustrialWastewaterprogrampermittingrequirementsonlyanddoesnotauthorizeoperationofthisfacilitypriortoobtaininganyotherpermitsrequiredbylocal,stateorfederalagencies.4.ThepermitteeshallprovideverbalnoticetotheDepartment'sNortheastDistrictOfficeassoonaspracticalafterdiscoveryofasinkholeorotherkarstfeaturewithinanareafori:bemanagementorapplicationofwastewater,orwastewatersludges.ThePermitteeshallimmediatelyimplementmeasuresappropriatetocontroltheentryofcontaminants,andshalldetailthesemeasurestotheDepartment'sNortheastDistrictOfficeinawrittenreportwithin7daysofthesinkholediscovery.[62-620.320(6)]28PERMITTEE:

JEA

PERMIT NUMBER:

FLOOO 1031-007

(Major) May

8, 2017 FACiliTY:

Northside Generating

Station

and

St. Johns

River Power

Park EXPIRATION

DATE: B.

. Specific Conditions

Related

to Existing Manufacturing,

Commercial,

Mining,

and Silviculture

Wastewater Facilities

or Activities 1. Existing manufacturing,

commercial,

mining,

and silvicultural

wastewater

facilities

or activities

that discharge into surface

waters

shall notify

the Department

as soon

as they know

or have reason

to believ

e: a. That

any activity

has occurred

or will occur which

would

result

in the discharge,

on

a routine

or frequent basis,

of any toxic pollutant

which

is not limited

in the permit,

if that discharge

will exceed

the highest

of the following

levels; (1)

One hundred micrograms

per liter, (2) Two hundred micrograms

per liter

for acrolein

and acrylonitrile;

five hundred micrograms

per liter

for 2, 4-dinitrophenol

and

for 2-methyl-4, 6-dinitrophenol;

and

one milligram

per liter

for antimony,

or (3) Five times

the maximum concentration

value reported

for that pollutant

in the permit application;

or b. That

any activity

has occurred

or will occur

which

would

result

in any discharge,

on

a non-routine

or infrequent

basis,

of

a toxic pollutant

which

is not limited

in the permit,

if that discharge

will exceed

the highest

of the following

levels; (1) Five hundred micrograms

per liter, (2)

One milligram

per liter

for antimony,

or (3)

Ten times

the maximum concentration

value reported

for that pollutant

in the permit application. C. Duty

to Reapply 1.

The permittee

is not authorized

to discharge

to waters

of the State

after

the expiration

date

of this permit,

unless

: a.

the permittee

has applied

for renewal

of this permit

at least

180 days before

the expiration

date (November, 9, 2016)

using

the appropriate

forms

listed

in Rule 62-620.910,

F.A.C.,

and

in the manner established

in the Department

of Environmental

Protection

Guide

to Permitting Wastewater

Facilities

or Activities

Under Chapter

62-620,

F.A.C., including

submittal

of the appropriate

processing

fee

set forth

in Rule 62-4.050, F.A.C.;

or b.

the permittee

has made complete

the application

for renewal

of this permit

before

the permit expiration

date. [62-620.335(1)-(4),

F

. A

. C.] 2. When publishing

Notice

of Draft

and Notice oflntent

in accordance

with Rules 62-110.106

and 62-620.550, F.A.C.,

the permittee

shall publish

the notice

at

its expense

in

a newspaper

of general circulation

in the county

or counties

in which

the activity

is

to take place

either a. Within

thirty

days

after

the permittee

has received

a notice

; or b. Within

thirty

days

after

final agency

action. Failure

to publish

a notice

is

a violation

of this permit D. Reopener

Clauses 1.

The permit

shall

be revised,

or alternatively,

revoked

and reissued

in accordance

with

the provisions

contained in Rules 62-620.325

and 62-620.345

F .A.

C.,

if applicable,

or

to comply

with

any applicable

eftluent

standard

or limitation

issued

or approved

under Sections 301(b)(2)(C)

and

(D), 304(b)(2)

and 307(a)(2)

of the Clean

Water Act

(the Act),

as amended,

if the eftluent standards, limitations,

or water quality standards

so issued

or approved: a. Contains

different conditions

or

is otherwise

more stringent

than

any condition

in the permit/or; b. Controls

any pollutant

not addressed

in the permit The permit

as revised

or reissued

under

this paragraph

shall contain

any other requirements

then applicable. 29PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:2.ThepennitmaybereopenedtoadjusteffluentlimitationsormonitoringrequirementsshouldfutureWaterQualityBasedEffluentLimitationdeterminations,waterqualitystudies,DEPapprovedchangesinwaterqualitystandards,EPAestablished TotalMaximumDailyLoads(TMDLs),orotherinformationshowaneedforadifferentlimitation,monitoringrequirement,ormorestringentrequirementsoranyapplicablestandardspertainingtotheoperationandmaintenanceofcoalcombustionwasteimpoundments.3.TheDepartmentorEPAmaydevelopaTMDLduringthelifeofthepennit.OnceaTMDLhasbeenestablishedandadoptedbyrule,theDepartmentshallrevisethispennittoincorporatethefmalfindingsoftheTMDL.4.Thepennitshallbereopenedforrevisionasappropriatetoaddressnewinformationthatwasnotavailableatthetimeofthispennitissuanceortocomplywithrequirementsofnewregulations,standards,orjudicialdecisionsrelatingtoCWA316(b).IX.GENERALCONDITIONS1.Theterms,conditions,requirements,limitationsandrestrictionssetforthinthispennitarebindingandenforceablepursuanttoChapter403,FloridaStatutes.AnypennitnoncomplianceconstitutesaviolationofChapter403,FloridaStatutes,andisgroundsforenforcementaction,permittermination,pennitrevocationandreissuance,orpennitrevision.[62-620.610(1)]2.Thispennitisvalidonlyforthespecificprocessesandoperationsappliedforandindicatedintheapproveddrawingsorexhibits.Anyunauthorizeddeviationsfromtheapproveddrawings,exhibits,specificationsorconditionsofthispennitconstitutesgroundsforrevocationandenforcementactionbytheDepartment.[62-620.610(2)]3.Asprovidedinsubsection403.087(7),F.S.,theissuanceofthispennitdoesnotconveyanyvestedrightsoranyexclusiveprivileges.Neitherdoesitauthorizeanyinjurytopublicorprivatepropertyoranyinvasionofpersonalrights,norauthorizeanyinfringementoffederal,state,orlocallawsorregulations.ThispennitisnotawaiveroforapprovalofanyotherDepartmentpennitorauthorizationthatmayberequiredforotheraspectsofthetotalprojectwhicharenotaddressedinthispennit.[62-620.610(3)]4.Thispennitconveysnotitletolandorwater,doesnotconstitutestaterecognitionoracknowledgmentoftitle,anddoesnotconstituteauthorityfortheuseofsubmergedlandsunlesshereinprovidedandthenecessarytitleorleaseholdinterestshavebeenobtainedfromtheState.OnlytheTrusteesoftheInternalImprovementTrustFundmayexpressStateopinionastotitle.[62-620.610(4)]5.Thispennitdoesnotrelievethepennitteefromliabilityandpenaltiesforharmorinjurytohumanhealthorwelfare,animalorplantlife,orpropertycausedbytheconstructionoroperationofthispermittedsource;nordoesitallowthepennitteetocausepollutionincontraventionofFloridaStatutesandDepartmentrules,unlessspecificallyauthorizedbyanorderfromtheDepartment.Thepermitteeshalltakeallreasonablestepstominimizeorpreventanydischarge,reuseofreclaimedwater,orresidualsuseordisposalinviolationofthispennitwhichhasareasonablelikelihoodofadverselyaffectinghumanhealthortheenvironment.Itshallnotbeadefenseforapennitteeinanenforcementactionthatitwouldhavebeennecessarytohaltorreducethepennittedactivityinordertomaintaincompliancewiththeconditionsofthispennit.[62-620.610(5)]6.Ifthepennitteewishestocontinueanactivity regulatedbythispennitafteritsexpirationdate,thepermitteeshallapplyforandobtainanewpermit.[62-620.610(6)]7.Thepennitteeshallatalltimesproperlyoperateandmaintainthefacilityandsystemsoftreatmentandcontrol,andrelatedappurtenances,thatareinstalledandusedbythepennitteetoachievecompliancewiththeconditionsofthispennit.Thisprovisionincludestheoperationofbackuporauxiliaryfacilitiesorsimilarsystemswhennecessarytomaintainorachievecompliancewiththeconditionsofthepennit.[62-620.610(7)]8.Thispennitmaybemodified,revokedandreissued,ortenninatedforcause.Thefilingofarequestbythepermitteeforapennitrevision,revocationandreissuance,ortermination,oranotificationofplannedchangesoranticipatednoncompliancedoesnotstayanypermitcondition.[62-620.610(8)]30PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)May8,2017FACILITY:NorthsideGeneratingStationandSt.JohnsRiverPowerParkEXPIRATIONDATE:9.Thepermittee,byacceptingthispermit,specificallyagreestoallowauthorizedDepartmentpersonnel,includinganauthorizedrepresentativeoftheDepartmentandauthorizedEPApersonnel,whenapplicable,uponpresentationofcredentialsorotherdocumentsasmayberequiredbylaw,andatreasonabletimes,dependinguponthenatureoftheconcernbeinginvestigated,to:a.Enteruponthepermittee'spremiseswherearegulatedfacility,system,oractivityislocatedorconducted,orwhererecordsshallbekeptundertheconditionsofthispermit;b.Haveaccesstoandcopyanyrecordsthatshallbekeptundertheconditionsofthispermit;c.Inspectthefacilities,equipment,practices,oroperationsregulatedorrequiredunderthispermit;andd.Sampleormonitoranysubstancesorparametersatanylocation necessarytoassurecompliancewiththispermitorDepartmentrules.[62-620.610(9)]10.Inacceptingthispermit,thepermitteeunderstandsandagreesthatallrecords,notes,monitoringdata,andotherinformationrelatingtotheconstructionoroperationofthispermittedsourcewhicharesubmittedtotheDepartmentmaybeusedbytheDepartmentasevidenceinanyenforcementcaseinvolvingthepermittedsourcearisingundertheFloridaStatutesorDepartmentrules,exceptassuchuseisproscribedbySection403.111,F.S.,orRule62-620.302,F.A.C.SuchevidenceshallonlybeusedtotheextentthatitisconsistentwiththeFloridaRulesofCivilProcedureandapplicableevidentiaryrules.[62-620.610(10)]11.WhenrequestedbytheDepartment,thepermitteeshallwithinareasonabletimeprovideanyinformationrequiredbylawwhichisneededtodeterminewhetherthereiscauseforrevising,revokingandreissuing,orterminatingthispermit,ortodeterminecompliancewiththepermit.ThepermitteeshallalsoprovidetotheDepartmentuponrequestcopiesofrecordsrequiredbythispermittobekept.IfthepermitteebecomesawareofrelevantfactsthatwerenotsubmittedorwereincorrectinthepermitapplicationorinanyreporttotheDepartment,suchfactsorinformationshallbepromptlysubmittedorcorrectionspromptlyreportedtotheDepartment[62-620.610(11)]12.UnlessspecificallystatedotherwiseinDepartmentrules,thepermittee,inacceptingthispermit,agreestocomplywithchangesinDepartmentrulesandFloridaStatutesafterareasonabletimeforcompliance;provided,however,thepermitteedoesnotwaiveanyotherrightsgrantedbyFloridaStatutesorDepartmentrules.Areasonabletimeforcompliancewithaneworamendedsurfacewaterqualitystandard,otherthanthosestandardsaddressedinRule62-302.500,F.A.C.,shallincludeareasonabletimetoobtainorbedeniedamixingzonefortheneworamendedstandard.[62-620.610(12)]·13.Thepermittee,inacceptingthispermit,agreestopaytheapplicableregulatoryprogramandsurveillancefeeinaccordancewithRule62-4.052,F.A.C.[62-620.610(13)]14.ThispermitistransferableonlyuponDepartmentapprovalinaccordancewithRule62-620.340,F.A.C.ThepermitteeshallbeliableforanynoncomplianceofthepermittedactivityuntilthetransferisapprovedbytheDepartment[62-620.610(14)]15.ThepermitteeshallgivetheDepartmentwrittennoticeatleast60daysbeforeinactivationorabandonmentofawastewaterfacilityoractivityandshallspecifywhatstepswillbetakentosafeguardpublichealthandsafetyduringandfollowinginactivationorabandonment.[62-620.610(15)]16.ThepermitteeshallapplyforarevisiontotheDepartmentpermitinaccordancewithRules62-620.300,F.A.C.,andtheDepartmentofEnvironmentalProtectionGuidetoPermittingWastewaterFacilitiesorActivitiesUnderChapter62-620,F.A.C.,atleast90daysbeforeconstructionofanyplannedsubstantialmodificationstothepermittedfacilityistocommenceorwithRule62-620.325(2),F.A.C.,forminormodificationstothepermittedfacility.ArevisedpermitshallbeobtainedbeforeconstructionbeginsexceptasprovidedinRule62-620.300,F.A.C.[62-620.610(16)]17.ThepermitteeshallgiveadvancenoticetotheDepartmentofanyplannedchangesinthepermittedfacilityoractivitywhichmayresultinnoncompliancewithpermitrequirements.Thepermitteeshallberesponsibleforany31PERMITTEE:JEAPERMITNUMBER:FL0001031-007(Major)MayS,2017FACILITY:NorthsideGenerating StationandSt.JohnsRiverPowerParkEXPIRATIONDATE:andalldamageswhichmayresultfromthechangesandmaybesubjecttoenforcementactionbytheDepartmentforpenaltiesorrevocationofthispermit.Thenoticeshallincludethefollowinginformation:a.Adescriptionoftheanticipatednoncompliance;b.Theperiodoftheanticipatednoncompliance,includingdatesandtimes;andc.Stepsbeingtakentopreventfutureoccurrenceofthenoncompliance.{62-620.610(17)]18.SamplingandmonitoringdatashallbecollectedandanalyzedinaccordancewithRule62-4.246andChapters62-160,62-601,and62-610,F.A.C.,and40CFR136,asappropriate.a.MonitoringresultsshallbereportedattheintervalsspecifiedelsewhereinthispermitandshallbereportedonaDischargeMonitoringReport(DMR),DEPForm62-620.910(10),orasspecifiedelsewhereinthepermit.b.Ifthepermitteemonitorsanycontaminantmorefrequentlythanrequiredbythepermit,usingDepartmentapprovedtestprocedures,theresultsofthismonitoringshallbeincludedinthecalculationandreportingofthedatasubmittedintheDMR.c.Calculationsforalllimitationswhichrequireaveragingofmeasurementsshalluseanarithmeticmeanunlessotherwisespecifiedinthispermit.d.ExceptasspecificallyprovidedinRule62-160.300,F.A.C.,anylaboratorytestrequiredbythispermitshallbeperformedbyalaboratorythathasbeencertifiedbytheDepartmentofHealthEnvironmentalLaboratoryCertificationProgram(DOHELCP).Suchcertificationshallbeforthematrix,testmethodandanalyte(s)beingmeasuredtocomplywiththispermit.Fordomesticwastewaterfacilities,testingforparameterslistedinRule62-160.300(4),F.A.C.,shallbeconductedunderthedirectionofacertifiedoperator.e.Fieldactivitiesincludingon-sitetestsandsamplecollectionshallfollowtheapplicablestandardoperatingproceduresdescribedinDEP-SOP-001/01adoptedbyreferenceinChapter62-160,F.A.C.f.AlternatefieldproceduresandlaboratorymethodsmaybeusedwheretheyhavebeenapprovedinaccordancewithRules62-160.220,and62-160.330,F.A.C.{62-620.610(18)]19.Reportsofcomplianceornoncompliancewith,oranyprogressreportson,interimandfmalrequirementscontainedinanycompliancescheduledetailedelsewhereinthispermitshallbesubmittednolaterthan14daysfollowingeachscheduledate.[62-620.610(19)]20.Thepermitteeshallreporttothe Department'sNortheastDistrictOfficeanynoncompliancewhichmayendangerhealthortheenvironment.Anyinformationshallbeprovidedorallywithin24hoursfromthetimethepermitteebecomesawareofthecircumstances.Awrittensubmissionshallalsobeprovidedwithinfivedaysofthetimethepermitteebecomesawareofthecircumstances.Thewrittensubmissionshallcontain:adescriptionofthenoncomplianceanditscause;theperiodofnoncomplianceincludingexactdatesandtime,andifthenoncompliancehasnotbeencorrected,theanticipatedtimeitisexpectedtocontinue;andstepstakenorplannedtoreduce,eliminate,andpreventrecurrenceofthenoncompliance.a.Thefollowingshallbeincludedasinformationwhichmustbereportedwithin24hoursunderthiscondition:(1)Anyunanticipatedbypasswhichcausesanyreclaimedwateroreflluenttoexceedanypermitlimitationorresultsinanunpermitteddischarge,(2)Anyupsetwhichcausesanyreclaimedwaterortheeffluenttoexceedanylimitationinthepermit,(3)Violationofamaximumdailydischargelimitationforanyofthepollutantsspecificallylistedinthepermitforsuchnotice,and(4)Anyunauthorizeddischargetosurfaceorgroundwaters.b.Oralreportsasrequiredbythissubsectionshallbeprovidedasfollows:(1)Forunauthorizedreleasesorspillsoftreatedoruntreatedwastewaterreportedpursuanttosubparagraph(a)4.thatareinexcessof1,000gallonsperincident,orwhereinformationindicatesthatpublichealthortheenvironmentwillbeendangered,oralreportsshallbeprovidedtotheSTATEWARNINGPOINTTOLL32(2)FREENUMBER(800)320-0519,assoonaspractical,butnolaterthan24hoursfromthetimethepermitteebecomesawareofthe discharge.Thepermittee,totheextentknown,shallprovidethefollowinginformationtotheStateWarningPoint:(a)Name,address,andtelephonenumberofpersonreporting;(b)Name,address,andtelephonenumberofpermitteeorresponsiblepersonforthedischarge;(c)Dateandtimeofthedischargeandstatusofdischarge(ongoingorceased);(d)Characteristicsofthewastewaterspilledorreleased(untreatedortreated,industrialordomesticwastewater);(e)Estimatedamountofthedischarge;(f)Locationoraddressofthedischarge;(g)Sourceandcauseofthedischarge;(h)Whetherthedischargewascontainedon-site,andcleanupactionstakentodate;(i)Descriptionofareaaffectedbythedischarge,includingnameofwaterbodyaffected,ifany;andG)Otherpersonsoragenciescontacted.(3}Oralreports,nototherwiserequiredtobeprovidedpursuanttosubparagraphb.labove,shallbeprovidedtotheDepartment'sNortheastDistrictOfficewithin24hoursfromthetimethepermitteebecomesawareofthecircumstances.c.Iftheoralreporthasbeenreceivedwithin24hours,thenoncompliancehasbeencorrected,andthenoncompliancedidnotendangerhealthortheenvironment,theDepartment'sNortheastDistrictOfficeshallwaivethewrittenreport.[62-620.610(20)}21.ThepermitteeshallreportallinstancesofnoncompliancenotreportedunderPermitConditionsIX.17,18or19ofthispermitatthetimemonitoringreportsaresubmitted.ThisreportshallcontainthesameinformationrequiredbyPermitConditionIX.20ofthispermit.[62-620.610(21)]22.BypassProvisions.a."Bypass"meanstheintentionaldiversionofwastestreamsfromanyportionofatreatmentworks.b.Bypassisprohibited,andtheDepartmentmaytakeenforcementactionagainstapermitteeforbypass,unlessthepermitteeaffmnativelydemonstratesthat:(1)Bypasswasunavoidabletopreventlossoflife,personalinjury,orseverepropertydamage;and(2)Therewerenofeasiblealternativestothebypass,suchastheuseofauxiliarytreatmentfacilities,retentionofuntreatedwastes,ormaintenanceduringnormalperiodsofequipmentdowntime.Thisconditionisnotsatisfiedifadequateback-upequipmentshouldhavebeeninstalledintheexerciseofreasonableengineeringjudgmenttopreventabypasswhichoccurredduringnormalperiodsofequipmentdowntimeorpreventivemaintenance;and(3)ThepermitteesubmittednoticesasrequiredunderPermitConditionIX.22.c.ofthispermit.c.Ifthepermitteeknowsinadvanceoftheneedforabypass,itshallsubmitpriornoticetotheDepartment,ifpossibleatleast10daysbeforethedateofthebypass.Thepermitteeshallsubmitnoticeofanunanticipatedbypasswithin24hoursoflearningaboutthebypassasrequiredinPermitConditionIX.20.ofthispeimit.Anoticeshallincludeadescriptionofthebypassanditscause;theperiodofthebypass,includingexactdatesandtimes;ifthebypasshasnotbeencorrected,theanticipatedtimeitisexpectedtocontinue;andthestepstakenorplannedtoreduce,eliminate,andpreventrecurrenceofthebypass.d.TheDepartmentshallapproveananticipatedbypass,afterconsideringitsadverseeffect,ifthepermitteedemonstratesthatitwillmeetthethreeconditionslistedinPermitConditionIX.22.b.1through3ofthispermit.e.Apermitteemayallowanybypasstooccurwhichdoesnotcausereclaimedwateroreffluentlimitationstobeexceededifitisforessentialmaintenancetoassureefficientoperation.ThesebypassesarenotsubjecttotheprovisionsofPermitConditionIX.22.b.throughd.ofthispermit.[62-620.610{22)]23.UpsetProvisions.33a."Upset"meansanexceptionalincidentinwhichthereisunintentionalandtemporarynoncompliancewithtechnology-basedeffluentlimitationsbecauseoffactorsbeyondthereasonablecontrolof1hepermittee.(I)Anupsetdoesnotincludenoncompliancecausedbyoperationalerror,improperlydesignedtreatmentfacilities,inadequatetreatmentfacilities,lackofpreventivemaintenance,carelessorimproperoperation.(2)AnupsetconstitutesanaffirmativedefensetoanactionbroughtfornoncompliancewithtechnologybasedpermiteffluentlimitationsiftherequirementsofupsetprovisionsofRule62-620.610,F.A.C.,aremet.b.Apermitteewhowishestoestablishtheaffrrmativedefenseofupsetshalldemonstrate,throughproperlysignedcontemporaneousoperatinglogs,orotherrelevantevidencethat:(I)Anupsetoccurredandthatthepermitteecanidentifythecause(s)oftheupset;(2)Thepermittedfacilitywasatthetimebeingproperlyoperated;(3)ThepermitteesubmittednoticeoftheupsetasrequiredinPermitConditionIX.20.bofthispermit;and(4)ThepermitteecompliedwithanyremedialmeasuresrequiredunderPermitConditionIX.20.ofthispermit.c.Inanyenforcementproceeding,theburdenofproofforestablishingtheoccurrenceofanupsetrestswiththepermittee.d.Beforeanenforcementproceedingisinstituted,norepresentationmadeduringtheDepartmentreviewofaclaimthatnoncompliancewascausedbyanupsetisfmalagencyactionsubjecttojudicialreview.[62-620.610(23)]ExecutedinTallahassee,Florida.34DivisionofWaterResourceManagement2600BlairStoneRoadTallahassee,Florida32399-2400

# DEPARTMENT OF ENVffiONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551,2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY:

LOCATION:

COUNTY:

OFFICE: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER:

MONITORING GROUP DESCRIPTION:

RE-SUBMITTED DMR: 

# 0

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: FL0001031-007-IW1S

Final REPORTFREQUENCY: Monthly

MA PROGRAM: Industrial

D-001

Combined discharge of NGS OTCW and SJRPP cooling tower blowdown.

________ To:

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Flow Sample

Measurement

P ARM C'ode 50050 1 Permit Report Report MGD 

# Hourly 

# Pump Logs

Mon SiteNo

. FLW-1 Requirement (Mo.Avg

. ) (Da,y.Max.)

Temperature 

# (F), Water (Intake) Sample

Measurement

PARM C'ode 00011 7 Permit Repmt Report Report DegF 

# C'ontinll()Ul; Meter

M:on Stte No. INT-1 Requitement (Day

. Mm

. ) (Mo

. Avg

. ) (Day.Max

. )

Temperature 

# (F), Water Sample

Measurement

PARM Code 00011 Q Permit Report Repmt 104 DegF 

# Continuous Meter

Mon

. Stte No. EFF-1 Reqmrement (Day

. Mm

. ) (MoAvg

. ) (Day Max)

Temp. Diff. between Intake and Sample

Discharge Measurement

PARM Code 61576 1 Permit Rt.port Repott 19 DegF 

# Continuous Calculated

Mon. Stte No EFF ' -1 Requirement (Day Min.) (MoAvg

. ) (Day Ma'-)

pH Sample

Measurement

PARM Code 00400 1 Permit 6

. 5 85 '».l1 

# Monthl)' Grab

Mon. Site No. EFF-1 ReqUllement (Day.Mm

. ) (Day.MaA

. )

Oxidants, Total Residual Sample

Measurement

PARM Code 34044 1 Permit 0.1 0.1 mg'L 

# Weekly Meter

Mon. Site No EFF-1 Requiremettt (Mo

. Avg

. ) (Day Max.)

TRO-Discharge Time Sample

Measuremettt

PARM Code04223 1 Permit 120 120 mini day 

# Daily, 24 hours Calculated

Mon. Site No. EFF-1 Requiremettt (Mo.Avg.) (Day

. Max.)

I certify under pettalty oflaw that this documettt and all attachmettts were prepared under my 

# direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gather.ng the information, the information submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant pettalties for submitting false information, including the possibility of fine and imprisonment for 

# knowing violations.

NAMFJTITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/ddlyyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attaclunents here):

1 

# Continuous monitoring of intake (INT -1) and discharge temperature (EFF-1) and temperature rise as required by Condition LA.l of the permit 

# shall be at least once per hour

ISSUANCFJREISSUANCE DATE: May 2012 D-001 Monthly Final Page 1 of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# FACILITY: 

# DISCHARGE MONITORING REPORT

- PART A (Continued)

Northside Generating Station and St Johns River Power Park MONITORING GROUP

NUMBER: D-001 PERMIT NUMBER: FL0001031-007-IWIS

MONITORING PERIOD From:

____ ____ ______ __ To:

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type



# Ex. Analysis

Copper, Total Recoverable Sample

(Intake) Measurement

PARM Code01119 7 Permit Report Report 

# ug/L Monthly 24-ht

· TPC

Mon. Site No. INT-I Requirement (Mo .o\vg.) (Day Max.)

Copper, Total Recoverable Sample

Measurement

PARMCode01119 1 Permit Report Report 

# ug/L Monthly 24-ht

· TPC

Mon. Site No EFF-lC Requirement (Mo.Avg) (Day.Max)

Iron, Total Recoverable Sample

(Intake) Measurement

PARM Code 00980 7 Permit Report Report 

# mgll Monthly 24-hrTPC

Mon. Site No. INT-I Requirement (Mo.Avg) (DavMax.)

Iron, Total Recoverable Sample

Measurement

PARM Code 00980 1 Permit Report Report 

# mg/L Monthly 24-hrTPC

Mon. Site No. EFF-lC Requirement (Mo.Avg.) (Dav.Max)

Mercury, Total Recoverable Sample

(Intake) Measurement

PARM Code 71901 7 Permit Report Report 

# ug/L Monthly 24-hrTPC

l'don. Site No. INT-I Requirement (Mo.Avg.) (Dav

. Max.)

Mercury, Total Recoverable Sample

Measurement

PARM Code 71901 1 Permit 0

. 025 0.025 

# ug/L Monthly 24-hrTPC

Mon. Site No

. EFF-IC Requirement (Mo.Avg.) (Day

. Max.)

Selenium, Total Recoverable Sample

(Intake) Measurement

P ARM Code 00981 7 Permit Report Report 

# ug/L Monthly 24-hrTPC'

Mon. Site No. INT-I Requirement (Mo.Avg.)**(Da~** 

# Max)

Selenium, Total Recoverable Sample

Measurement

P ARM Code 00981 1 Permit 

# 71 71 

# ug/L Monthly 24-hrTPC

Mon. Site No. EFF-IC Requirement (Mo.Avg.) (Dav

. Max.)

Specific Conductance Sample

Measurement

PARM Code 00095 1 Permit Report Report 

# umhos/cm Monthly 24-hrTPC'

Mon. Site No. EFF-1 Requirement (Mo.Avg.) (Dav.Ma11:.)

7-DAYCHRONIC STATRE Sample

Mysidopsis bahia (Routine) Measurement

PARM Code TRP3E 

# p Permit 100 percent 

# Quarterly 24-hrTPC

Mon. Site No. EFF-1 Reauirement (Min.)

7-DA Y CHRONIC ST ATRE Sample

Mysidopsis bahia (Additional) Measurement

PARM Code TRP3E Q Permit 100 pen:ent 

# As needed As required by

Mon. Site No. EFF-1 Reauirement (Min.) the permit

7-DAY CHRONIC STATRE Sample

Mysidopsis bahia (Additional) Measurement

PARM Code TRP3E R Permit 100 pen:ent 

# A!. needed As requh-ed by

Mon. Site No. EFF-1 Requirement (Min.) the permit

ISSUANCFIREISSUANCE DATE: May 2012 D-001 Monthly Final Page2 of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DISCHARGE MONITORING REPORT

- PART A (Continued)

FACILITY: Northside Generating Station and St. Johns River Power Park MONITORING GROUP

NUMBER: D-001

MONITORING PERIOD From:

______________ __

Parameter Quantity or Loading Units Quality or Concentration

7-DA Y CHRONIC STATRE Menidia Sample

beryllina (Routine) Measurement

PARM Code TRP6B 

# p Permit 100

Mon

. Site No EFF-1 Requirement (Mm..)



# 7-DAY CHRONIC STATRE Menidia Sample

beryllina (Additional) Measurement

PARM Code TRP6B Q Permit 100

Mon. Srte No

. EFF-1 Requirement (Mm

. )

7-DAY CHRONIC STATRE Menidia Sample

beryllina (Additional) Measurement

PARM Codf TRP6B R Pet mit 100

M:on

. Stte No 

# EFF-1 Requit etneitt (Min

. )

ISSUANCE/REISSUANCE DATE: May 2012 D-001 Monthly Final Page3 of3 PERMIT NUMBER: FL0001031-007-IW1S

To:

Units No. Frequency of Sample Type

Ex. Analysis

percent 

# Quarterly 24-hrTPC

peroont 

# As 

# needed As 

# requtred by

the permit

petcent 

# As needed 

# M. required by

the



# · oermit

DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY: 

# JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033 PERMIT NUMBER:



# LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FL0001031-007-IWIS

Final

MA

D-001 REPORT FREQUENCY:

PROGRAM: Semi-annually

Industrial

LOCATION: Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive MONITORING GROUP DESCRIPTION: Combined discharge ofNGS OTCW and SJRPP cooling tower blowdown.

Jacksonville, FL 32226-3033



# COUNTY: Duval

OFFICE: Northeast District

Parameter Quantity or Loading

Aluminum, Total Recoverable Sample

Measurement

PARM Code 0 1104 1 Permit

Mon. Site No. EFF-IC Requirement

Arsenic, Total Recoverable Sample

Measurement

PARM Code 00978 1 Permit

Mon. Site No. EFF-1 C Requirement

Chromium, Total Recoverable Sample

Measurement

PARMCode01118 1 Permit

Mon. Site No. EFF-1C ReQuirement

Lead, Total Recoverable Sample

Measurement

PARM Code01114 1 Permit

Mon. Site No. EFF-IC Requirement

Nickel, Total Recoverable Sample

Measurement

PARM Code 01074 I Perm i t

Mon. Site No

. EFF-1C Requirement

Silver, Total Recoverable Sample

Measurement

PARM Code 01079 I Permit

Mon. Site No. EFF-IC Requirement

Zinc, Total Recoverable Sample

Measurement

PARM Code 01094 I Permit

Mon. Site No. EFF-1C Requirement RE-SUBMITTED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From:

________ To:

Units Quality or Concentration

Report Report

(Mo.Avg) (Day 

# Max.)

36 36

(Mo.Avg) (Day.Max.)

Report Report

(Mo.Avg.) (Day.Max)

Report Report

(Mo.Avg.) (Day.Mn.)

Report Report

(Mo.A,·g.) (Day Max.)

Report Report

(Mo

. Avg.) (Day

. Max.)

Report Report

(MoAvg.) (Day.Max.) Units No. Frequency of Sample Type

Ex. Analysis



# ug/L Semi-Annually ; 24-hrTPC

twice per 

# year



# ug/L Semi-Annually ; 24-hrTPC

twice 

# per year



# ug/L Semi-Annually; 24-hrTPC

twice per year



# ug/L Semi-Annually; 24-hrTPC

twice per year



# ugll. Semi-Annually; 24-hrTPC

twice pet year



# ug/L Semi-Annually; 24-hrTPC

twice per year



# ug/L Semi-Annually: 24-hrTPC

twice pet yea r

I certify under penalty of law that this document and all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false infonnation, including the: possibility of fine and imprisonment for knowing violations.

NAMFJTITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/ddlyyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):



# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

ISSUANCEIREISSUANCE DATE: May 2012 D-001 Semiannually Final Page I of I DEP Fonn 62-620.910(10), Effective Nov. 29, 1994

# When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033 PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FL0001031-007-lW1S

Final

MA

D-010 REPORT FREQUENCY:

PROGRAM: Monthly

Industrial

LOCATION: Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive MONITORING GROUP DESCRIPTION: NGS Emergency Percolation Pond Overflow.

Jacksonville, FL 32226-3033

COUNTY: Duval

OFFICE: Northeast District

Parameter Quantity or Loading

Flow Sample

Measurement

P ARM Code 50050 I 

# Permtt Report

Mon

. Site No f ' LW-10 Requit-ement (Da:y Max)

Duration of Discharge Sample

Measurement

PA.RM Code 81381 I 

# Permit Report

Mon

. Site No EFF-10 Requirement (Da:yMa")

Solids, Total Suspended Sample

Measurement

PARM Code 00530 I 

# Permit

Mon

. Site No

. FFF-10 Requitement

Oil and Grease Sample

Measurement

PARM Code 00556 1 Permit

Mon

. Site No EFF-10 Requirement

Arsenic, Total Recoverable Sample

Measurement

PARM Code 00978 1 Permit

Mon

. Site Jl.io EFF-10 Requirement

Cadmium, Total Recoverable Sample

Measurement

PARMCode01113 1 Permit

Mon. Site No EFF-10 Requirement

Chromium, Total Recoverable Sample

Measurement

PARM Code01118 1 Permit

Mon Site No EFF-10 Requirement RE-SUBMITTED DMR: 

# 0

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: --------To:

Units Quality or Concentration

MGD

hr•da)



# Report

(Da)'

. Ma11.)

Report

(Da:y

. Ma11..)

Report

(Da:y.Max.)

Report

(Day.Max)

Report

(Day.Ma11.) Units

mg!l

mgil



# ug/L

ug/L

ug/L 

# No. Frequency of Sample Type

Ex. Analysis

Daily, when Estimated

dilichatlting

Daily

, 111ohen Estimated

di8Charj!jng

Daily, when Gtab

di&charging

Daily

, when Grab

discharging

Daily, when Gtab

di&charging

Dail:y

, when Grab

dischargmg

Daily, when Grab

discharging

I certify under penalty of law that this document and all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, to the best of my knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAMEfi'ITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/dd/yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 D-010 Monthly Final Page2of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# FACILITY: DISCHARGE MONITORING REPORT- PART A (Continued)

Northside Generating Station and St Johns River Power Park MONITORING GROUP D-0 

# 10

NUMBER : PERMIT NUMBER: FL0001031-007-IWIS

MONITORING PERIOD From :

-------- To :

Parameter Quantity or Loading Units Quality or 

# Concentration Units No. Frequency of Sample Type

Ex. Analysis

Iron, Total Recoverable Sample

Measurement

PARM Code 00980 1 Permit Report ug/L 

# Daily, when Grab

Mon. Site No

. EFF-10 Requirement (Day.Max) discharging

Copper, Total Recoverable Sample

Measurement

PARM Code 01119 1 Permit Report ug/L 

# Dail)'

, when Grab

Mon. Site No. EFF-10 Requirement (Day.Max-l discharstinl!:

Lead, Total Recoverable Sample

Measurement

PARM Code01114 1 Permit Report ug/L 

# Dail)', when G!ab

Mon. Site No

. EFF-10 Requirement (Day.Max)

**discha~** 

# Mercury, Total Recoverable Sample

Measurement

PARM Code 71901 

# 1 Permit Report ug/L 

# Daily, when Grab

Mon

. Site No. EFF-10 Requirement (Day

. Max) discharging

Nickel, Total Recoverable Sample

Measurement

PARM Code01074 1 Permit Report ug/L 

# Daily, when Grab

Mon

. Site No

. EFF-10 Requirement (Day

. Max

. ) d i scharging

Zinc, Total Recoverable Sample

Measurement

PARM Code01094 1 Permit Report ug/L 

# Daily, when Grab

Mon

. Site No

. EFF-10 Requirement (Da}

. Max

. ) discharging

pH Sample

Measurement

PARM Code 00400 1 Permit Report s.u. 

# Daily, when Grab

Mon

. Site No

. EFF-10 Requirement (Day.Max.) dischargina

ISSUANCEIREISSUANCE DATE: May 2012 D-010 Monthly Final Page 3 of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551,2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY:

LOCATION:

COUNTY:

OFFICE: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER:

MONITORING GROUP DESCRIPTION:

RE-SUBMITTED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: FL0001031-007-IWIS

Final REPORT FREQUENCY:

MA PROGRAM:



# D-Oll

NGS Emergency Pond Overflow

________ To: Monthly

Industrial

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Flow Sample

Measurement

PARM Code 50050 I**Pe~mit** 

# Report MGD 

# Daily, when btimated

Mon Site No

. FLW-11 Requireinent (Dav

. Max

. ) diSCharl!:IDJ!:

Duration of Discharge Sample

Measurement

PARM Code 81381 1 Permit Report hr'day 

# Dail)'

, 

# when**E~timated** 

# Mon. Site 'No. EFF-11 Requireinent (Day Max

. ) dischargmg

Solids, Total Suspended Sample

MeasUreinent

P ARM Code 00530 1 Permit Report mg/L 

# Dail}'

, when Grab

Mon SiteNo EFF-11 Requireinent (Da}'

. Milll.) di&ehargmg

Oil and Grease Sample

Measurement

PARM Code 00556 1 Permit Report mg/1 

# Dai1}'

, when Grab

Mon. Site N"o. EFF-11 Requireinent (Day Max.) discharging

Arsenic, Total Recoverable Sample

Measurement

P ARM Code 00978 1 Permit Report ug'L 

# Daily

, whm Grab

Mon. Site No EFF-11 Requil'einent (Day Max) dischargmg

Cadmium, Total Recoverable Sample

MeasUreinent

PARM Code 01113 1 Permit Report ugiL 

# Daily

, when Grab

Mon Site No. EFF-11 Requirement (Day.Max) discharging

Chromium, Total Recoverable Sample

MeasUreinent

PARM Code 01118 1 Permit Report**ug~I** 

# Daily, when Grab

Mon. Site 'No EFF-11 Requireinent (Day Max) discharging

I certify under penalty of law that this document and all attachments were prepared under my direction or supervision in accordance with a systein designed to 

# assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the systein, or those persons directly responsible for gathering the information, the information submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAMFII1TLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNA TIJRE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mrnlddlyyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Refermce all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 D-Oll 

# Monthly Final Page 1 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DISCHARGE MONITORING REPORT- PART A (Continued)

FACILITY: 

# Northside Generating Station and St Johns River Power Park

Parameter Quantity or Loading

Iron, Total Recoverable Sample

Measurement

PARM Code 00980 1 Permit

Mon. Site No. EFF-11 Requirement

Copper, Total Recoverable Sample

Measurement

PARM Code 01ll9 1 

# Permit

Mon

. Site No. EFF-11 Requirement

Lead, Total Recoverable Sample

Measurement

PARM Code01114 1 Permit

Mon. Site No. EFF-11 Requirement

Mercury, Total Recoverable Sample

Measurement

PARM Code 71901 1 Permit

Mon Site No. EFF-11 Requirement

Nickel, Total Recoverable Sample

Measurement

PARM Code01074 1 Permit

Mon. Site No. EFF-11 Requirement

Selenium, Total Recoverable Sample

Measurement

P ARM Code 00981 l Permit

Mon. Site No EFF-11 Requirement

Zinc, Total Recoverable Sample

Measurement

PARM Code 01094 l Permit

Mon. Site No

. EFF-11 Requirement

pH Sample

Measurement

PARM Code 00400 l Permit

Mon. Site No. EFF-11 Requirement

ISSUANCEIREISSUANCE DATE: May 2012 D-Oll 

# MONITORING GROUP

NUMBER:

MONITORING PERIOD

Units

Monthly D-Oll PERMIT NUMBER: FL000103l-007-IWIS

From:

______________ __ To :

Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Report ug/L 

# Daily, when Grab

(Day.Max.) dischargmg

Report ug/L 

# Daily, when Grab

(Day Max.) discharging

Report ug/L 

# Daily, when Grab

(Day.Max

. ) discharging

Report ug/L 

# Daily, when Grab

(Day.Max

. ) discharging

Report ug/L 

# Daily, when Grab

(Day

. Max

. ) discharging

Report ug/L 

# Daily, when Grab

(Day 

# Max

. ) discharging

Report ug/L 

# Daily, when Grab

· (Day .Max.) dischargmg

Report s.u. 

# Daily, when Grab

(Day

. Max.) discharging

Final Page2 of2 DEP Form 62-620

. 910(10)

, Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY:

LOCATION:



# COUNTY:

OFFICE: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER:

MONITORING GROUP DESCRIPTION:

RE-SUBMITTED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: FL0037869-007-IWB

Final

MA

D-002 REPORT FREQUENCY:

PROGRAM:

SJRPP Runoff Sedimentation Control Pond.

________ To: Quarterly

Industrial

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Flow Sample

Measurement

PARM Code 50050 I 

# Permit Report Report MGD 

# Quarterly Calculated

Mon Site No EFF-2 Requirement (Mo

. Avg.) (Da)'.Max.)

Solids, Total Suspended Sample

Measurement

P ARM Code 00530 I Permit 50 0 500 rng/l 

# Quarterly Grab

1\.fon Site No EFF-2 Requirement (Mo.Avg) (Day.Mn.)

Oil and Grease Sample

Measurement

P ARM Code 00556 I 

# Permit 5

. 0 5.0 rng'L 

# Quarter!)' Grab

Mon. Site No. EFF-2 Reqw1

· ement**~Mo.Avg)** 

# (Day.Max)

pH Sample

Measurement

P ARM Code 00400 I Permit 6.5 8.5 J.U 

# Quarterly GJab

Mon S1teNo EFF-2 Requirement (Da}'.Min

. ) (Day Max)

I certify under penalty of law that this docwnent and all attachments were prepared under my direction or supervision in accordance with a system designed 

# to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted 

# is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAME/TITLE OF PRINCIPAL EXECUTIVE OFFICER OR AliTHORIZED AGENT SIGNATURE OF PRINClPAL EXECUTIVE OFFICER OR AliTHORIZED AGENT TELEPHONE NO DATE (rnrn/ddlyyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 D-002 Monthly Final Page 1 of1 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551,2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY:

LOCATION:

COUNTY:

OFFICE: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER:

MONITORING GROUP DESCRIPTION:

RE-SUBMITTED DMR: 

# 0

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: FL0037869-007-IWB

Final REPORT FREQUENCY:

MA PROGRAM:

D-004

SJRPP Coal Pile Runoff Sedimentation Pond

________ To: Monthly

Industrial

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Flow Sample

Measurement

PARM Code 50050 1 Permit Report MGD 

# Per discharge Calculated

Mon. Site No. FLW-4 Requirement (Day.Max.)

Duration of Discharge Sample

Measurement

PARM Code 81381 

# I Permit Report min 

# Per discharge Calculated

Mon

. Site No. EFF-4 Requirement (Day .Max.)

Solids, Total Suspended Sample

Measurement

PARM Code 00530 1 Permit Report mg/L 

# Per discharge Grab

Mon. Site No. EFF-4 Reqwrement (Day.Max.)

Aluminum, Total Recoverable Sample

Measurement

PARM Code01104 

# I Permit 1.5 mg/L 

# Per discharge Grab

Mon. Site No EFF-4 Requrrement (Day Max.)

Arsenic, Total Recoverable Sample

Measurement

P ARM 

# Code 00978 

# I Permit 50 mg/L 

# Per discharge Grab

Mon. Site No. EFF-4 Requirement (Day

. Max.)

Chromium, Total Recoverable Sample

Measurement

1 

# PARM Code01118 1 Permit Report mg/L 

# Pe1 discharge Grab

Mon. Site No

. 

# EFF-4 Requirement (Day .Max.)

Copper, Total Recoverable Sample

Measurement

PARM Code 01119 

# I Permit 3.7 mg/L 

# Per discharge Grab

Mon

. Site No

. EFF-4 Requirement (Day.Max.)

I certify under penalty of law that 

# this document and all attachments were prepared under my direction or supervision 

# in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or thos·!l persons directly responsible for gathering the information, the information submitted is, to the best of my

knowledge and belief, 

# true, accurate, and complete. I am aware that there are significant penalties 

# for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAME/TITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mrnlddlyyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 D-004 Monthly Final Page 

# I of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# FACILITY : 

# DISCHARGE MONITORING REPORT- PART A (Continued)

Northside Generating Station and St. Johns River Power Park MONITORING GROUP D-004



# NUMBER : PERMIT NUMBER: FL0037869-007-IWB

MONITORING PERIOD From:

__ __ _ __ _ To :

Parameter Quantity or Loading Units Quality or Concentration Units No

. Frequency of Sample Type

Ex

. 

# Analysis

Iron, 

# Total Recoverable Sample

Measurement

P <\.RM Code 00980 1 Permit 0.3 mg/L 

# Pet discharge Grab

Mon Site No

. EFF-4 Requirement (Day.Mn.)

Lead, 

# Total Recoverable Sample

Measurement

PARM Code01114 1 Permit 

# 85 mg·L 

# Pet discharge Gtab

Mon. Site No EFF-4 Requirement (Day

. Max

. )

Mercury, Total Recoverable Sample

Measurement

PARM Code 71901 I 

# Permit 0

. 025 mg/L 

# Pet di!>Charge Grab

Mon. Site No

. EFF-4 Requirement (Da}

. Max

. )

Nickel, Total Recoverable Sample

Measurement

PARM Code 01074 1 Pel'mit 

# 83 mgtl. 

# Pe r discharge Gtab

Mon Site "No. EFf-4 Requirement (Day Max.)

Selenium, Total Recoverable Sample

Measurement

P



# . "-RM Code 00981 1 Permit 71 mg!L 

# Pet

**di~charge** 

# Grab

Mon 8Ite No

. EFf'-4 Requirement (Da}.Mn)

Silver, Total Recoverable Sample

Measurement

P <\.RM Code 01079 1 Permit Report mg

· 'L 

# Pet discharge Gtab

Mon Site No EFF-4 Requirement (Da)

. MBA)

Zinc, Total Recoverable Sample

Measurement

P

,

<\.RM Code 01094 1 Petmit 

# 86 mg:L 

# Pet

· dischlllge Crtab

Mon. Site No. EFF-4 Requirement (Day Max)

pH Sample

Measurement

P ARM Code 00400 1 Permit 6.5 

# 8.5

**~.u**

**.** 

# Per discharge Grab

Mon S1te No. F.Ff-4 Requirement (Day Min) (DayMn

. )

ISSUANCEIREISSUANCE DATE: May 2012 D-004 Monthly Final Page2 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT· PART A

When Completed mail this report 

# to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY:

LOCATION:



# COUNTY:

OFFICE: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER:

MONITORING GROUP DESCRIPTION:

RE-SUBMITTED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: FL0037869-007-1WB

Final

MA

D-009 REPORT FREQUENCY:

PROGRAM:

SJRPP Solid Waste Runoff Sedimentation Pond Discharge.

________ To: Monthly

Industrial

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Flow Sample

Measurement

PARM Code 50050 1 Permit Report MGD 

# Per discharge Calculated

Mon. Site No. FLW-9 Requirement (Day.Max.)

Duration of Discharge Sample

Measurement

PARM Code 81381 1 Permit Report min 

# Per discharge Meter

Mon. Site No. EFF-9 Requirement (Day.Max.)

Solids, Settleable Sample

Measurement

PARM Code 00545 1 Permit Report mUL 

# Per discharge Grab

Mon. Site No. EFF-9 Requirement (Day Max.)

Solids, Total Dissolved (IDS) Sample

Measurement

PARM Code 70295 1 Permit Report mg/L 

# Per discharge Grab

Mon. Site No. EFF-9 Requirement (Day.Max.)

Solids, Total Suspended Sample

Measurement

PARM Code 00530 1 Permit Report mg/L 

# Per discharge Grab

Mon. Site No. EFF-9 Requ i rement (Day.Max.)

Aluminum, Total Recoverable Sample

Measurement

PARM Code 01104 1 Permit 1.5 mg/L 

# Per discharge Grab

Mon. Site :No. EFF-9 Requirement (Day

. Max.)

Arsenic, Total Recoverable Sample

Measurement

PARM Code 00978 1 Permit 50 ug/L 

# Per discharge Grab

Mon

. Site No. EFF-9 Requirement (Day.Max

. )

I certify under penalty of law that this document and all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted 

# is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties 

# for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAME/TITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/dd/yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCE/REISSUANCE DATE: May 2012 D-009 Monthly Final Page 1 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# FACILITY: 

# DISCHARGE MONITORING REPORT

- PART A (Continued)

Northside Generating Station and St Johns River Power Park MONITORING GROUP D-009

NUMBER : PERMIT NUMBER: FL0037869-007-IWB

MONITORING PERIOD From :

- --- --- - To :

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. 

# Analysis

Chromium, Total Recoverable Sample

Measurement

PARM C'ode0lll8 

# 1 Permit Report ug'L 

# Per discharge Grab

Mon. Site No EFF-9 Requirement (Day

. Max)

Copper, Total Recoverable Sample

Measurement

PARM Code0lll9 1 Permit 37 ug/l 

# Per :

**di&~o:harge** 

# Grab

Mon Site No. EFF-9 Requirement (Da)

. Max)

Iron, Total Recoverable Sample

Measurement

PARM Code 00980 

# 1 Permit 0.3 mg/L 

# Per

**di~charge** 

# Glab

l'vfon Srte No. EFF-4 Requirement (Da).Max

. )

Lead, Total Recoverable Sample

Measurement

PARM C'ode01114 

# 1 Permit 

# 8

. 5 uq'l· 

# Per

**di~charge** 

# GI

· ab

Mon. Site No EFF-9 Reqwrement (Day.Mn)

Mercury, Total Recoverable Sample

Measurement

PARM Code 71901 1 Permit 0.025 ug/L 

# Per

**di~charge** 

# Grab

Mon Stte No EFF-9 Requtrement (Da) .MilA

. )

Nickel, Total Recoverable Sample

Measurement

P ARM Code 01074 

# 1 Permit 83 ug1

. 

# Per discharge 

# G n lb

Mon Site No EFF-9 Requirement (Day .Max)

Selenium, Total Recoverable Sample

Measurement

PARM Code Q0981 I Permit 71 ug'L 

# Per discharge Glab

Mon. Site No EFF-9 Requirement (Day

. Max.)

Silver, Total Recoverable Sample

Measurement

PARM Code 01079 1 Permit Report ug'L 

# Per discharge Grab

Mon Site No. EFF-9 Reqwrcment (Day.Max

. )

Zinc, Total Recoverable Sample

Measurement

P ARM Code 01094 1 Permit 86 ug'L 

# Pet

**dt~luuge** 

# GI

· ab

Mon

. Site No EFF-9 Requirement (Day Max.)

pH Sample

Measurement

PARM Code 00400 1 Permit 6.0 90 s.u 

# Pe1

**di~charge** 

# Grab

Mon Stte No EFF-9

**Require~nent** 

# (Day.Min

. ) (Day MilA.)

ISSUANCEIREISSUANCE DATE: May 2012 D-009 Monthly Final Page2 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report 

# to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033 PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FLD037869-007-IWB

Final

MA

I-001 REPORT FREQUENCY:

PROGRAM: Monthly

Industrial

LOCATION: Northside Generating Station and St Johns River Power Park

4377 Heckscher Drive MONITORING GROUP DESCRIPTION: SJRPP Cooling Tower Blowdown and Central Wastewater Treatment

Jacksonville, FL 32226-3033

COUNTY: Duval



# OFFICE: Northeast District

Parameter Quantity or Loading

Flow Sample

Measurement

PARM Code 50050 

# I Permit Report Rep01t

Mon

. Site No. FLW-2 Requirement (Mo.Avg) (Da'l Max)

Flow Sample

Measurement

PARM Code**~0050** 

# Q Permit Report Report

Mon. Site No. FLW-3 Requirement (Mo

. Avg.) (Da'i

. Max

. )

Oxidants, Total Residual Sample

Measurement

PARM Code 34044 

# p Permit

Mon. Site No. OUI-1 Requirement

TRO-Discharge Time Sample

Measurement

PARM Code04223 

# p Permit

Mon. Site No. OUI-1 Requirement

Cycles of Concentration Sample

Measurement

PARM Code 51463 

# p Permit

Mon. Site No. OUI-1 Requirement

Specific Conductance Sample

Measurement

PARM Code 00095 

# p Permit

Mon. Site No. OUI-1 Requirement

Temperature (F), Water Sample

Measurement

PARMCodeOOOll 

# p Permit

Mon

. Site No. OUI-1 Requirement RE-SUBMITTED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: --------To:

Units Quality or Concentration

MGD

MGD



# 0.01 0.01

(Mo.Avg.) (DayMn.)

120 120

(Mo.Avg.) (Day

. Max.)

1.5

(Day_Max.)

Report

(Day.Max.)

Report 96.0

(Mo_Avg

. ) (Day.Max.) Units No. Frequency of Sample Type

Ex. 

# Analysis

Daily ; 24 hours Pump Logs

Daily, 24 hours**PumpLo~**



# mg/L Weekly Grab

min/day Weekly Meter

cycles Monthly Calculated

umhostcm Monthly 24-hrTPC

DegF 

# Continuow. Calculated

I certify under penalty of law that this document and all attachments were prepared under 

# my direction or supervision in accordance with a system designed 

# to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, 

# to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAME/TITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/dd.'yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 I-001 Monthly Final Page 1 of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# FACILITY : 

# DISCHARGE MONITORING REPORT· PART A (Continued)

Northside Generating Station and St Johns River Power Park MONITORING GROUP

NUMBER : D-001 PERMIT NUf\.1BER: FL0037869-007-IWB

MONITORING PERIOD From :

---------------- To :

Parameter Quantity or Loading Units Quality or Concentration Units No

. Frequency of Sample Type



# Ex. Analysis

pH Sample

Measurement

PARM Code 00400 

# p Permit 6

. 5 8.5

**~.U** 

# Monthly Grab

Mon Site No OUI-1 Requirement (Da}' Min) (Da}'Max.)

Arsenic, Total Recoverable Sample

Measurement

PARM Code00978 

# p Permit Report Report ug/l 

# Monthly

, when 

# Grab

M:on Site No

. OUI-1 Requirement (Mo.Avg) (DayMax) discharging_

Mercury, Total Recoverable Sample

Measurement

PARM Code ? l901 

# p Permit Report Report

**u~l** 

# Monthl}'

, when 

# Grab

Mon. Site No

. OUI-1 Requirement (Mo.Avg.) (Day

. Mn

. ) discharging

Selenium, Total Recoverable Sample

Measurement

P ARM Code 00981 

# p Permit Report Report ug/L 

# Monthly

, when Grab

Mon

. Site No

. OUI-1 Requirement (Mo.Avg) (DayMn

. ) discharging

Nitrogen, Ammonia, Total (as N) Sample

Measurement

PARM Code 00610 

# p Permit Report Report mg/L 

# Weekly, when Grab

Mon

. Site No

. OUI-1 Requirement (Mo

. Avg.) (Day

. Max) dischargmg

Nitrogen, Ammonia, Total (as 

# N) Sample

Measurement

P ARM Code 00610 

# Q Permit Report Report mg/l. 

# Weekly, when 

# Grab

Mon

. Site No

. INT-2 Requirement (Mo.Avg) (Day

. Max) discharging

Nitrogen, Kjeldahl, Total (as N) Sample

Measurement

PARM Code 00625 

# p Permit Report Report mg.l 

# Weekly, when Gtab

Mon. Site No. Ol.Jl-1 Requirement (Mo.Avg.) (Day.Max) diSCharging

Nitrogen, Kjeldahl, Total (as N) Sample

Measurement

P-'\RM Code 00625 

# Q Permit Report Report mg/l 

# Weekly

, when Grab

M:on

. Site No. INT-2 Requirement (MoAvg.) (Day

. Mn) discharging

Nitrite plus Nitrate, Total 1 det. (as N) Sample

Measurement



# - PARM Code 00630 

# p Permit Report Report mg > l

. 

# Weekl}'

, when Gtab

Mon. Site No Olll-1 Requirement (Mo

. Avg

. ) (Da)

. Mn.) dischargmg

Nitrite plus Nitrate, Total 1 det

. (as 

# N) Sample

Measurement

PARM Code 00630 

# Q Permit Report Report mgll 

# Monthly

, when Grab

Mon

. Site No INT-2 Requirement (Mo.Avg.) (Day

. Mn

. ) dtscharging

Nitrogen, Total Sample

Measurement

PARM Code 00600 

# p Pennit Report Repott mg/L 

# Weekly

, when Calculated

Mon. Stte No

. OUI-1 Requirement (Mo.Avg

. ) (Day. Max

. ) discharging

ISSUANCEIREISSUANCE DATE: May 2012 1-001 Monthly Final Page2 of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# FACILITY : DISCHARGE MONITORING REPORT-PART A (Continued)

Northside Generating Station and St. Johns River Power Park MONITORING GROUP

**~0** 

# 1

NUMBER : PERMIT NUMBER: FL0037869-007-1WB

MONITORING PERIOD From :

-------- To :

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Nitrogen, Total Sample

Measurement

P ARM Code 00600 Q Permit Report Report mg/L 

# Weekly, when Calculated

Moo Site No. INl-2 Requirement (Mo.Avg) (Day.Max) discharging

Nitrogen, Total Sample

(Monthly Net Loading) Measurement

PARM Code 00600 R 

# Permit Report lblmth 

# Monthly, when Calculated

Mon. Site No

. OUI-1 Requirement (Mo. Total) discharging

Nitrogen, Total Sample

(Annual 

# Net Loading) Measurement

P ARM Code 00600 

# T Permit Report lb!yr 

# Monthly, when Calculated

Mon. Site No. OUI-1 Requirement (An 

# Total) dischargtng

ISSUANCEIREISSUANCE DATE: May 2012 1-001 Monthly Final Page 3 of3 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551,2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITIEE NAME:

MAILING ADDRESS:

FACILITY: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033 PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FL0037869-007-IWB

Final

MA

I-005 REPORT FREQUENCY:

PROGRAM: Monthly

Industrial

LOCATION: Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive MONITORING GROUP DESCRIPTION: SJRPP Combined Cooling Tower Blowdowns from Units 1 and 2

Jacksonville, FL 32226-3033



# COUNTY: Duval

OFFICE: Northeast District

Parameter Quantity or Loading

Flow Sample

Measurement

PARM Code 

# 50050 1 Permit Report Report

Mon

. Site No- FLW-5 Requirement (Mo_Avg.) (DayMa") RE-SUBMITIED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From:

________ To:

Units Quality or Concentration

MGD 

# Units No. Frequency of Sample Type

Ex. Analysis

Daily

, 24 hours Pump Logs

I certify under penalty of law that this document and all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAME/TITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/ddlyyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCFJREISSUANCE DATE: May 2012 I-003 Monthly Final Page 1 of 1 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report 

# to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551,2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMI'ITEE NAME:

MAILING ADDRESS:

FACILITY: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033 PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FL0037869-007-IWB

Final

MA

I-006 REPORT FREQUENCY :

PROGRAM: Monthly

Industrial

LOCATION: Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive MONITORING GROUP DESCRIPTION: Central Wastewater Treatment Facility

Jacksonville, FL 32226-3033

COUNTY: Duval

OFFICE: Northeast District

Parameter Quantity or Loading

Flow Sample

Measurement

PARM Code 50050 I Permit Report Report

Mon. Site No. FLW-6 Requirement (Mo.Avg.) (Day

. Max.)

Solids, Total Suspended Sample

Measurement

PARM Code 00530 p 

# Permit

Mon. Site No

. OUI-6 Requirement

Solids, Total Suspended Sample

Measurement

P ARM Code 00530 Q Permit 1920.0

Mon

. Site No. OUI-6 Requirement (Day.Max)

Oil and Grease Sample

Measurement

P ARM Code 00556 p 

# Permit

Mon. Site No. OUI-6 Requirement

Oil and Grease Sample

Measurement

PARM Code00556 Q Permit 260.0

Mon. Site No

. OUI-6 Requirement (Day

. Ma'l(

. )

pH Sample

Measurement

PARM Code 00400 p 

# Permit

Mon. Site No

. OUI-6 Requirement

Length 

# of Longest pH Excursion Sample

Measurement

PARM Code 72107 p 

# Permit

Mon. Site No OUI-6 Requirement RE-SUBMI'ITED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From:

________ To:

Units Quality or Concentration

MOD



# 30.0 50.0

(Mo

. Avg

. ) (Day.Max

. )

lblclay



# 15.0 20.0

(Mo.Avg.) (Day.Ma'l(.)

lblday



# 6.0 9.0

(Day

. Min.) (Day.Max.)

446 60

(Mo

. Total) (Day.Max

. ) 

# ' Units No. Frequency of Sample Type

Ex. Analysis

Daily; 24 hours Meter

mg/L 

# Monthly 24-hrTPC

Monthly Calculated

mg!L 

# Monthly Grab

Monthly Calculated

s.u. Continuous Recorder

min 

# Continuous Recorder

I certify under penalty of law that this document and all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the infonnation submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties 

# for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAME/TITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (rnrnldd/yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCE'REISSUANCE DATE: May 2012 I-006 Monthly Final Page 1 of2 DEP Fonn 62-620.910(10), Effective Nov. 29, 1994

# FACILITY: DISCHARGE MONITORING REPORT

- PART A (Continued)

Northside Generating Station and St. Johns River Power Park MONITORING GROUP I-006

NUMBER: PERMIT NUMBER: FL0037869-007-IWB

MONITORING PERIOD From:

_______ _ 

# .To:

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Copper, Total Recoverable Sample

Measurement

PARM Code01119 p 

# Permit 1.0 10 mgtL 

# Monthly 24-hrTPC

Mon

. Site No OUI-6 Reqmrement (Mo.Avg

. ) (Day

. Max.)

Iron, Total Recoverable Sample

Measurement

PARM Code 00980 p 

# Permit 1.0 I 0 mg. I 

# Monthly 24-hrTPC

Mon

. Site No. Ol.JI-6 Requirement (Mo

. Avg) (Day.Mall)

Silver, Total Recoverable Sample

Measurement

PARM Code 01079 p 

# Permit 0.0064 0.0064 ugll 

# Monthly 24-ht TPC

Mon

. Stte No

. OUI-6 Requirement (Mo

. Avg

. ) (Day .Max

. )

Selenimn, Total Recoverable Sample

Measurement

P ARM Code 00981 p 

# Permit Report Report ugll 

# Monthly, when 24-ht TPC

Mon Site No

. OUI-6 Requirement (Mo.Avg

. ) (Day.Max.

. ) di&"Cluirgmg

Phosphorus, Total (asP) Sample

Measurement

PARM Code 00665 p 

# Permit Report 10 mg-L 

# Pee Application 24-ht

· TPC

Mon

. Stte No. OUI-6 Requirement (Mo

. Avg

. ) (Day

. Max

. )

Nitrogen, Kjeldahl, Total (as N) Sample

Measurement

PARM Code 00625 p 

# Permit Repmt Report mg/L 

# Monthly

, when 24-hl TPC

Mon

. Stte No. OUI-6 Requirement (Mo.Avg

. ) (Day

. M11A

. ) di&"Charging

Nitrite plus Nitrate, Total 1 det. (as N) Sample

Measurement

PARM Code 00630 p 

# Permit Repol't Report mg/L 

# Monthly

, when 24-hl

· TPC

Mon

. 'Stte No. OUI-6 Requirement (Mo

. Avg.) (Day

. Max

. ) discluirging

Nitrogen, Anrmonia, Total (as N) Sample

Measurement

PARM Code 00610 p 

# Permit Repmt Report mgtL 

# Monthly, when 24-hl rPC

Mon. Site No. OUI-6 Requirement (Mo.Avg

. ) (Day

. MaA

. ) di!seharging

Nitrogen, Total Sample

Measurement

PARM Code 00600 p 

# Permit Report Report mgll 

# Monthly, when 24-hl TPC'

Mon

. Site No

. Ol.JI-6 Requitement (Mo

.. Avg)**(Day Ma"~**  

# di&"Charging

Nitrogen, Total Sample

(Monthly Loading) Measurement

P ARM Code 00600 

# Q Permit Report !bimth 

# Monthly

, when 

# C' alculated

Mon. Stte No OUI-6 Requirement (MoTotal) discharging

ISSUANCEIREISSUANCE DATE: May 2012 I-006 Monthly Final Page2 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mall this report to: Department of Environmental Protection

, Wastewater Compliance Evaluation Section, MS 3551

, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMmEE NAME :

MAILING ADDRESS :

FACILITY :

LOCATION:

COUNTY:

OFFICE : 

# JEA

4377 Heckscher Drive

Jacksonville, 

# FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District PERMIT NUMBER :

LIMIT :

CLASS SIZE:

MONITORING GROUP NUMBER :

MONITORING GROUP DESCRIPTION:

RE-SUBMmED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From: FL0037869-007-IWB

Final

MA

I-006 REPORT FREQUENCY:

PROGRAM:

Central Wastewater Treatment Facility

________ To : Quarterly

Industrial

Parameter Quantity or Loading Units Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Mercury, Total Recoverable Sample

Measurement

PARM Code 71901 

# p Permit Report Report ug!L 

# Quarterly, when

Mon. Site No

. OUI-6 Reqwrement (Mo.Avg.) (Day.Max.) discharging

I certify under penalty of law that this document and 

# all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, to the best of my knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations

. Grab

NAMEfi'ITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/dd/yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

lSSUANCEIREISSUANCE DATE: May 2012 I-006 Quarterly Final Page 1 of1 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report 

# to: Department of Environmental Protection, Wastevrater Compliance Evaluation Section, MS 3551, 2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMmEE NAME:

MAILING ADDRESS:

FACILITY: JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033 PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FL0001031-007-IWIS

Final



# MA

R-001 REPORT FREQUENCY:

PROGRAM: Monthly

Industrial

LOCATION: Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive MONITORING GROUP DESCRIPTION: NGS Evaporation/ Percolation Pond Land Application System.

Jacksonville, FL 32226-3033

COUNTY: Duval

OFFICE: Northeast District

Parameter Quantity or Loading

Flow Sample

Measurement

PARM Code 50050 't 

# Petmit Report

Mon S1te No

. EFF-4 Reqwrement (An.Av!!;)



# Flow Sample

Measurement

PARM Code 50050 I Petmit Report Repott

Mon

. S1te No EFF-4 Requirement (Mo.Avg

, ) (Day Max)

Flow Sample

Measurement

PARM Code 50050 Q Permit Report

Mon. Site No PPI-1 ReqUirement (An.Avg)

Flow Sample

Measurement

PI\RM Code 50050 R Permit Report Rep01t

Mon S1te No. PPI-1 Requirement fMo

. AvJ!;

. ) (Day.Max

. )

pH Sample

Measurement

PARM Code 00400 1 Petmit

Mon. :Site No

. EFF-4 Requitement

pH Sample

Measurement

PARM Code00400 Q Petmit

Mon

. Site No. PPI-1 Requirement

Solids, Total Dissolved (TDS) Sample

Measurement

P ARM Code 70295 1 Petmit

Mon S1te }ljo

. EFF-4 Requirement

Solids, Total Dissolved (TDS) Sample

Measurement

PARM Code 70295 Q Permit

Mon Site No. PPI-1 Requirement RE-SUBMmED DMR: 

# D

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From:

________ To:

Units Qua li ty or Concentration

MGD

MGD

MGD

MGD



# 6.5 

# 8.5

(Da)'

. Min

. ) (Da'(.Max

. )

Rep01t Report

(Day

. Min) (Day Max

. )

Report

(Day .Max.)

Report

(Day.Ma>.

. ) Units No. Frequency of Sample Type



# Ex. Analysis

Daily, 24 hours Calculated

Daily ; 

# 14 hol!I'li Calculated

Daily ; 24 hours Calculated

Daily

, 24 hours Calculated

&.U 

# 5 Day&IWeek Grab**~-U** 

# 5 Days/Week Grab**m~I L**  

# Monthly 24-lu TPC

mg, L 

# Monthly 24-hrTPC

I certify under penalty of law that this document and all attachmet1ts were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAMFJTITLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE 

# (mm/dd'yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 R-001 Monthly Final Page 1 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# DISCHARGE MONITORING REPORT

- PART A (Continued)

FACILITY: Northside Generating Station and St Johns River Power Park

Parameter Quantity or Loading

Specific Conductance Sample

Measurement

P ARM 

# Code 00095 1 Permit

Mon. Site No. EFF-4 Requirement

Specific Conductance Sample

Measurement

PARM Code 00095 Q Permit

Mon. Site No. PPI-1 Requirement

Lead, Total Recoverable Sample

Measurement

PARM Code 01114 

# I Permit

Mon. Site No. EFF-4 Requirement

Lead, Total Recoverable Sample

Measurement

PARM Code 01114 Q Permit

Mon. Site No

. PPI-1 Requirement

Nickel, Total Recoverable Sample

Measurement

PARMCode01074 1 Permit

Mon. Site No. EFF-4 Requirement

Nickel, Total Recoverable Sample

Measurement

PARM Code01074 Q Permit

Mon. Site No. PPI-1 Requirement

Sodium, Total Recoverable Sample

Measurement

PARM Code 00923 1 Permit

Mon. Site No. EFF-4

. Requirement

Sodium, Total Recoverable Sample

Measurement

PARM Code 00923 Q Permit

Mon. 8ite No. PPl-1 Requirement

Turbidity Sample

Measurement

PARM Code 00070 l Permit

Mon. Site No

. EFF-4 Requirement

Turbidity Sample

Measurement

PARM Code 00070 Q Permit

Mon. 

# Site No

. PPI-1 Requirement

Vanadium, Total Recoverable Sample

Measurement

PARMCode01128 1 Permit

Mon. Site No. EFF-4 Requirement

Vanadium, Total Recoverable Sample

Measurement

PARM Code01128 Q Pet mit

Mon. Site No. PPI-1 Requirement

ISSUANCEIREISSUANCE DATE: May 2012 R-001 MONITORING GROUP

NUMBER:

MONITORING PERIOD

Units

Monthly R-001 PERMIT NUMBER: FL0001031-007-IW1S

From:

-- ------------ -- To:

Quality or Concentration Units No. Frequency of Sample Type

Ex. Analysis

Report umhos/cm Monthly 24-hrTPC

(Day.Max.}

Report umhos/cm Monthly 24-hrTPC

(Day.Max.)

Report ug/L Monthly 24-hrTPC

(Day.Max.)

Report ug!L Monthly 24-hrTPC

(Day MID..}



# Report ug/L Monthly 24-hrTPC

(Da}.Max.}

Report ug!L Monthly 24-hrTPC

(Da'f

. Max.}

Report mgll Monthly 24-ht TPC

(Day

. Max.)

Report mg!L Monthly 24-ln

· fPC

(Day .Max.}

Report NTU 

# Monthly 24-hrTPC

(Day Max.}

Report NTU 

# Monthly 24-hrTPC

(Da'(.Max}

Report ug"L Monthly 24-hrTPC

(Day.Max

. )

Report ug/L Monthly 24-hrTP(:

(Day.Max.)

Final Page2 of2 DEP Form 62-620.910(10}, Effective Nov. 29, 1994

# DEPARTMENT OF ENVIRONMENTAL PROTECTION DISCHARGE MONITORING REPORT- PART A

When Completed mail this report to: Department of Environmental Protection, Wastewater Compliance Evaluation Section, MS 3551,2600 Blair Stone Road, Tallahassee, FL 32399-2400

PERMITTEE NAME:

MAILING ADDRESS:

FACILITY:

LOCATION:

COUNTY:

OFFICE:

Parameter JEA

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Northside Generating Station and St. Johns River Power Park

4377 Heckscher Drive

Jacksonville, FL 32226-3033

Duval

Northeast District

Quantity or Loading

Nitrite plus Nitrate, Total! det. (as N) Sample

Measurement

P ARM C'ode 00630 I**Pe~mit** 

# Mon. S1te No

. EFF-4 Requirement

Nitrite plus Nitrate, Total I det. (as N) Sample

Measurement

P ARM Code 00630 Q Permit

Mon

. Site No. PPI-1 Requireme!lt

Sulfate, Total Sample

Measurement

PARM Code 00945 

# 1 Permit

Mon. S1te No 

# EFF -4 Requitement

Sulfate, Total Sample

Measurement

PARM Code 00945 Q Permit

Mon. Site No. PPI-1 Requireme!lt PERMIT NUMBER:

LIMIT:

CLASS SIZE:

MONITORING GROUP NUMBER: FLOOOI031-007-IW1S

Final

MA

R-001 REPORT FREQUENCY:

PROGRAM: Quarterly

Industrial

MONITORING GROUP DESCRIPTION: NGS Evaporation/ Percolation Pond Land Application System.

RE-SUBMITTED DMR: 

# 0

NO DISCHARGE FROM SITE: 

# 0

MONITORING PERIOD From:

________ To:

Units Quality or Concentration

Report

(Day.Mn

. )

Report

(Day

. Max)

Report

(Day 

# .Max)

Report

(Day.Mall:) Units

mg'lmgll

.

mg/J.

.

mg/L 

# No. Frequency of Sample Type

Ex. Analysis

Quarterly 24-ht TPC

Quarterly 24-ht TPC

Quarterly 24-ht TPC

Quarterly 24-ht fPC

I certify under penalty oflaw that this document and all attachments were prepared under my direction or supervision in accordance with a system designed to assure that qualified personnel properly gather and evaluate

the information submitted. Based on my inquiry of the person or persons who manage the system, or those persons directly responsible for gathering the information, the information submitted is, to the best of my

knowledge and belief, true, accurate, and complete. I am 

# aware that there are significant penalties for submitting false information, including the possibility of fine and imprisonment for knowing violations.

NAMErfiTLE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT SIGNATURE OF PRINCIPAL EXECUTIVE OFFICER OR AUTHORIZED AGENT TELEPHONE NO DATE (mm/dd/yyyy)



# COMMENT AND EXPLANATION OF ANY VIOLATIONS (Reference all attachments here):

ISSUANCEIREISSUANCE DATE: May 2012 R-001 Quarterly Final Page 1 of 1 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# INSTRUCTIONS FOR COMPLETING THE WASTEWATER DISCHARGE MONITORING REPORT

Read these instructions before completing the DMR. Hard copies and/or electronic copies of the required parts of the DMR were provided with the pennit. All required information shall be completed in full and typed or printed

in ink. A signed, original DMR shall be mailed to the address printed on the DMR by the 28th of the month following the monitoring period. The DMR shall not be submitted before the end of the monitoring 

# period

The DMR consists of three parts-A, B, and D--all of which may or may not be 

# applicable to every facility. Facilities may have one or more Part A's for reporting eftluent or reclaimed water data. All domestic wastewater facilities

will have a Part B for reporting daily sample results. Part D is used for reporting ground water monitoring well data.

When results are not available, the following codes should be 

# used on parts A and D of the DMR and an explanation provided where appropriate. Note: Codes used on Part B for raw data are different.

CODE DESCRIPTION/INSTRUCTIONS CODE DESCRIPTION/INSTRUCTIONS

ANC Analysis not conducted. NOD No discharge from/to site.

DRY 

# Dry Well OPS Operations were shutdown so no sample could be taken.

FLO Flood disaster. OTH Other. Please enter an explanation of why monitoring data were not available.

IFS Insufficient flow for sampling. SEF Sampling equipment failure.

LS Lost sample.

MNR Monitoring not required this period.

When reporting analytical results that fall below a laboratory's reported method detection limits or practical quantification limits, the following instructions should be 

# used:

I. Results greater than or equal to the PQL shall be reported as the measured quantity.

2. Results less than the PQL and greater 

# than or equal to the MDL shall be reported as the laboratory's MDL value. These values shall be deemed equal to the MDL when necessary to calculate an average for that parameter and

when determining compliance with permit limits.

3. Results less 

# than the MDL shall be 

# reported by entering a less than sign ("<") followed by the laboratory's MDL value, e.g. < 0.00 1. A value of one-half the MDL or one-half the eftluent limit, whichever is lower, shall be

used for that sample when necessary to calculate an average for that parameter. Values less 

# than the MDL are considered to demonstrate compliance with an eftluent limitation.

PART A -DISCHARGE MONITORING REPORT (DMR)

Part A of the DMR is comprised of one or more sections, each having its own header information. Facility information is preprinted in the header as well as the monitoring group number, whether the limits and monitoring

requirements are interim or fmal, and the required submittal frequency (e.g. monthly, annually, quarterly, etc.). Submit Part A based on the required reporting frequency in the header and the instructions shown in the permit. The

following should be completed by the permittee or authorized representative:

Resubmitted DMR: Check this box if this DMR is being re-submitted because there was information missing from or information that needed correction on a previously submitted DMR. The information that is being revised

should be clearly noted on the re-submitted DMR (e.g. highlight, circle, etc.)

No Discharge From Site: Check this box if no discharge occurs and, as a result, there are no data or codes to be entered for all of the parameters on the DMR for the entire monitoring group number; however, if the monitoring

group includes other monitoring locations (e.g., influent sampling), the ''NOD" code should be used to individually denote those parameters for which there was no discharge.

Monitoring Period: Enter the month, day, and year for the first and last day of the monitoring period (i.e. the month, the quarter, the year, etc.) during which the data on this report were collected and analyzed.

Sample Measurement: Before filling in sample measurements in the table, check to see that the data collected correspond to the limit indicated on the DMR (i.e. interim or final) and that the data correspond to the monitoring

group number in the header. Enter the data or calculated results for each parameter on this row in the non-shaded area above the limit. Be sure the result being entered corresponds to the appropriate statistical base code (e.g.

annual average, monthly average, single sample maximum, etc.) and units.

No. Ex.: Enter the number of sample measurements during the monitoring period that exceeded the permit limit for each parameter in the non-shaded area. If none, enter zero.

Frequency of Analysis: The shaded areas in this column contain the minimum number of times the measurement is required to be made according to the permit. Enter the actual number of times the measurement was made in the

space above the shaded area.

Sample Type: The shaded areas in this column contain the type of sample (e.g. grab, composite, continuous) required by the permit. Enter the actual sample type that was taken in the space above the shaded area.

Signature: This report must be signed in accordance with Rule 62-620.305, F.A.C. Type or print the name and title of the signing official. Include the telephone number where the official may be 

# reached in the event there are

questions concerning this report. Enter the date when the report is signed.

Comment and Explanation of Any Violations: Use this area to explain any exceedances, any upset or by-pass events, or other items which require explanation. If more space is needed, reference all attachments in this area.

ISSUANCEIREISSUANCE DATE: May 2012 DMR Instructions Page 1 of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994

# PART B- DAILY SAMPLE RESULTS

Monitoring Period: Enter the month, day, and year for the 

# first and last day of the monitoring period (i.e. the month, the quarter, the year, 

# etc.) during which the data on this report were collected and analyzed.

Dally Monitoring Results: Transfer all analytical data from your facility's laboratory or a contract laboratory's data sheets for all day(s) that samples were collected

. Record the data in the units indicated

. Table I in Chapter 62-



# 160, F.AC

. , contains a complete list of all the 

# data qualifier codes 

# that your laboratory may use when reporting analytical results. However, when transferring numerical results onto Part 

# B of the DMR, only the following data

rfi od h ld 

# b used d

· ·ded wh

· qua 1 ere es s ou e an an explanation proVJ ere_lllll)ropnate.

CODE DESCRIPTION/INSTRUCTIONS



# < The compound was analyzed for but not detected.

A Value reported is the mean (average) of two or more determinations.

J Estimated value, value not accurate

. 

# Q Sample held beyond the actual holding time.



# y Laboratory analysis 

# was from an unpreserved or improperly preserved sample.



# . . To calculate the monthly average, add each reported value to get a total. For flow, dJVJde th1s total by the number of days in the month. For all other parameters, divide the total by the number of observations

. Plant Staffing: List the name, certificate number, and class of all state certified operators operating the facility during the monitoring period. Use additional sheets as necessary.

PART D- GROUND WATER MONITORING REPORT

Monitoring Period: Enter the month. day, and year for the 

# frrst and last day of the monitoring period (i.e. the month, the quarter, the year, etc.) during which the data on this report were collected and analyzed.

Date Sample Obtained: Enter the date the sample 

# was taken. Also, check whether or not the well 

# was purged before sampling.

Time Sample Obtained: Enter the time the sample was taken.

Sample Measurement: Record the results of the analysis. If the resuh was below the minimum detection limit, indicate that.

Detection Limits: Record the detection limits of the analytical methods used.

Analysis Method: Indicate the analytical method used. Record the method number from Chapter 62-160 or Chapter 62-601, F.A.C., or from other sources. Sampling Equipment Used: Indicate the procedure used to collect the sample (e.g. airlift, bucket/bailer, centrifugal pump, etc.)

Samples Filtered: Indicate whether the sample obtained was filtered by laboratory (L), filtered in field (F), or unfiltered 

# (N).

Signature: This report must be signed in accordance with Rule 62-620.305, F.A.C. Type or print the name and title of the signing official. Include the telephone number where the official may be reached in the event there are questions concerning this report. Enter the date when the report is signed.

Comments and Explanation: Use this space to make any comments on or explanations of resuhs that are unexpected. If more space is needed, reference all attachments in this area

.



# .

SPECIAL INSTRUCTIONS FOR LIMITED 

# WET WEATHER DISCHARGES

Flow (Limited Wet Weather Diseharge): Enter the measured average flow rate during the period of discharge or divide gallons discharged by duration of discharge (converted into days). Record in million gallons per day

(MGD)

. Flow (Upstream): Enter the average flow rate in the receiving stream upstream from the point of discharge for the period of discharge. The average flow rate can be calculated based on two 

# measurements; one made at the start

and one made at the end of the discharge period

. Measurements are to be made at the upstream gauging station described in the permit.

Actual Stream Dll.ution Ratio: To calculate the Actual Stream Dilution Ratio, divide the average upstream flow rate by the average discharge flow rate. Enter the Actual Stream Dilution Ratio accurate to the nearest 0.1.

No. of Days the SDF 

# > Stream Dilution Ratio: For each day of discharge, compare the minimum Stream Dilution Factor (SDF) from the permit to the calculated Stream Dilution Ratio. On 

# Part B of the DMR, enter an asterisk



# (*) if the SDF is greater than the Stream Dilution Ratio on any day of discharge. On 

# Part A of the DMR, add up the days with an 

# "*" and record the total number of days the Stream Dilution Factor was greater than the Stream

Dilution Ratio.

CBOD

5 : 

# Enter the average CBOD

5 

# of the reclaimed water discharged during the period shown in duration of discharge.

TKN: Enter the average TKN of the reclaimed water discharged during the period shown in duration of discharge.

Actual Rainfall: Enter the actual rainfall for each day on Part B. Enter the actual cumulative rainfall to date for this calendar year and the actual total monthly rainfall on Part A. The cumulative rainfall to date for this calendar

year is the total amount of rain, in inches, that has been recorded since January 1 of the current year through the month for which this DMR contains data

Rainfall During Average RainfaU Year: On 

# Part A, enter the total monthly rainfall during the average rainfall year and the cumulative rainfall for the average rainfall year

. The cumulative rainfall for the average rainfall year is

the amount of rain, in inches, which fell during the average rainfall year from January through the month for which this DMR contains data.

No. of Days L WWD Activated During Calendar Year: Enter the cumulative number of days that the limited wet weather discharge was activated since January I of the current year.

Reason for Discharge: Attach to the DMR a brief explanation of the factors contnbuting to the need to activate the limited wet weather discharge.

ISSUANCEIREISSUANCE DATE: May 2012 DMR Instructions Page2of2 DEP Form 62-620.910(10), Effective Nov. 29, 1994