Name: Shih Chieh Lin

Title: Plant General Manager

Company: TEMES (Cabras No. 1 & 2 PMC)

Sign Date:

Name: Tony Wong

Title: President

Company: AirKinetics Inc.

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Emissions Testing Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, July 06, 2011 Page 1 of 19
Emissions Testing Unit 1

Facility Information:

Cabras Power Plant

No. 322 Cabras Hwy, Route 11

Piti GU 96915

Contact: Melinda R. Camacho

Phone: (671) 648-2312

Fax: (671) 648-3167

Email: plant.mgr@temes.com.tw

Testing Company:

AirKinetics Inc.

1308 S. Allec

Anaheim CA 92805

Contact:Tony Wong

Phone: (714) 245-1945

Fax: (714) 956-2350

Email: wongt@airkineticsinc.com

Air Permit Number:

FO-002

Permitted Source ID/Name:

Cabras # 1 Boiler Unit # 1

Permitted Maximum Process Rate:

Title V Air Permit has no limit on MM

Max. Normal Operation Process Rate:

481 MMBtu/hr

Target Process Test Rat

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: N/A FRS #: N/A

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 113.69 0 0 113.69 480 1212 2 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Carbon

stack Method 25A 3 120 0

stack Total PM2.5 OTM - 27/28 3 367 0

stack Filterable PM2.5 OTM - 27/28 3 367 0

Regulation Description Compound Limit Unit

Wednesday, July 06, 2011 Page 2 of 19
Emissions Testing Unit 1

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Organic Condensible 

Particulate

stack OTM - 27/28 3 367 0

Inorganic (Aqueous) 

Condensible Part.

stack OTM - 27/28 3 367 0

stack Total Particulate OTM - 27/28 3 367 0

stack Filterable Particulate OTM - 27/28 3 367 0

stack Arsenic Method 29 3 240 0

stack Antimony Method 29 3 240 0

stack Beryllium Method 29 3 240 0

stack Cadmium Method 29 3 240 0

stack Chromium Method 29 3 240 0

stack Cobalt Method 29 3 240 0

stack Lead Method 29 3 240 0

stack Manganese Method 29 3 240 0

stack Nickel Method 29 3 240 0

stack Selenium Method 29 3 240 0

stack O2 Method 3A O2 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack Filterable Particulate Method 5 240 0

stack Sulfur Dioxide Method 6C 3 120 0

stack Nitrogen oxides (NOx) Method 7E 3 120 0

Wednesday, July 06, 2011 Page 3 of 19
Emissions Testing Unit 1

Sampling / Stack Data Results Summary

Location stack - Method 10

Average

Run Number 1 2 3

Test Date 1/20/2011 1/20/2011 1/21/2011

Run Start Time 11:13:00 AM 1:48:00 PM 10:01:00 AM

Run Finish Time 1:13:00 PM 3:48:00 PM 12:01:00 PM

Carbon Dioxide, % 11.74 11.72 11.65 11.703

Oxygen, % 6.2 6.27 6.24 6.237

Dry Volumetric Flow Rate, dry scfm 136576 128782 137514 134,290.667

F-Factor, dscfm/MMBtu @ %O2 9258 9258 9305 9,273.667

Moisture, % 12.41 12.83 12.12 12.453

Fuel Type Override Override Override

Fw

Fc

Location stack - Method 25A

Average

Run Number 1 2 3

Test Date 1/20/2011 1/20/2011 1/21/2011

Run Start Time 11:13:00 AM 1:48:00 PM 10:01:00 AM

Run Finish Time 1:13:00 PM 3:48:00 PM 12:01:00 PM

Carbon Dioxide, % 11.74 11.72 11.65 11.703

Oxygen, % 6.2 6.27 6.24 6.237

Dry Volumetric Flow Rate, dry scfm 136576 128782 137514 134,290.667

F-Factor, dscfm/MMBtu @ %O2 9258 9258 9305 9,273.667

Moisture, % 12.41 12.83 12.12 12.453

Fuel Type Override Override Override

Fw

Fc

Wednesday, July 06, 2011 Page 4 of 19
Emissions Testing Unit 1

Location stack - Method 29

Average

Run Number 2 3 4

Test Date 1/19/2011 1/20/2011 1/21/2011

Run Start Time 12:10:00 PM 12:18:00 

PM

3:30:00 PM

Run Finish Time 4:27:00 PM 4:57:00 PM 7:46:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 165.672 163.327 170.534 166.511

Moisture Content of Stack Gas, % 12.27 12.82 12.43 12.507

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.72 11.74 11.49 11.650

Oxygen, % 6.27 6.26 6.29 6.273

Average Stack Gas Temperature, °F 354.17 357.71 358.17 356.683

Dry Volumetric Flow Rate, dry scfm 129,023.3 128,777.7 133,174.8 130,325.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 226,929.8 228,917.9 235,812.5 230,553.400

Percent Isokinetic of Sampling Rate, % 101.5 101.0 101.2 101.233

F-Factor, dscfm/MMBtu @ %O2 9688 9258 9305 9,417.000

Fw

Fc

Wednesday, July 06, 2011 Page 5 of 19
Emissions Testing Unit 1

Location stack - Method 5

Average

Run Number 2 3 4

Test Date 1/19/2011 1/20/2011 1/21/2011

Run Start Time 12:10:00 PM 12:18:00 

PM

11:49:00 AM

Run Finish Time 4:27:00 PM 4:57:00 PM 7:46:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 165.672 163.327 170.534 166.511

Moisture Content of Stack Gas, % 12.27 12.82 12.43 12.507

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.72 11.74 11.49 11.650

Oxygen, % 6.27 6.26 6.29 6.273

Average Stack Gas Temperature, °F 354.17 357.71 358.17 356.683

Dry Volumetric Flow Rate, dry scfm 129,023.3 128,777.7 133,174.8 130,325.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 226,929.8 228,917.9 235,812.5 230,553.400

Percent Isokinetic of Sampling Rate, % 101.5 101.0 101.2 101.233

F-Factor, dscfm/MMBtu @ %O2 9688 9258 9305 9,417.000

Fw

Fc

Location stack - Method 6C

Average

Run Number 1 2 3

Test Date 1/21/2011 1/21/2011 1/21/2011

Run Start Time 10:01:00 AM 1:01:00 PM 3:47:00 PM

Run Finish Time 12:01:00 PM 3:01:00 PM 5:47:00 PM

Carbon Dioxide, % 11.65 11.69 11.65 11.663

Oxygen, % 6.24 6.22 6.28 6.247

Dry Volumetric Flow Rate, dry scfm 137514 137514 133190 136,072.667

F-Factor, dscfm/MMBtu @ %O2 9305 9305 9305 9,305.000

Moisture, % 12.12 12.12 12.43 12.223

Fuel Type Override Override Override

Fw

Fc

Wednesday, July 06, 2011 Page 6 of 19
Emissions Testing Unit 1

Location stack - Method 7E

Average

Run Number 1 2 3

Test Date 1/21/2011 1/21/2011 1/21/2011

Run Start Time 10:01:00 AM 1:01:00 PM 3:47:00 PM

Run Finish Time 12:01:00 PM 3:01:00 PM 5:47:00 PM

Carbon Dioxide, % 11.65 11.69 11.65 11.663

Oxygen, % 6.24 6.22 6.28 6.247

Dry Volumetric Flow Rate, dry scfm 137514 137514 133190 136,072.667

F-Factor, dscfm/MMBtu @ %O2 9305 9305 9305 9,305.000

Moisture, % 12.12 12.12 12.43 12.223

Fuel Type Override Override Override

Fw

Fc

Location stack - OTM - 27/28

Average

Run Number 2 3 4

Test Date 1/19/2011 1/20/2011 1/21/2011

Run Start Time 7:40:00 AM 7:31:00 

AM

9:06:00 AM

Run Finish Time 2:17:00 PM 2:48:00 PM 3:37:00 PM

Net Run Time, minutes 364.7141317 368.264478

1

371.5

Dry Gas Meter Volume Sampled, dscf 123.433 128.568 129.865 127.289

Moisture Content of Stack Gas, % 12.08 12.41 12.11 12.200

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.76 11.74 11.67 11.723

Oxygen, % 6.28 6.26 6.23 6.257

Average Stack Gas Temperature, °F 349.25 353.92 356.00 353.057

Dry Volumetric Flow Rate, dry scfm 136,078.0 136,566.8 138,031.4 136,892.067

Actual Wet Volumetric Flue Gas Flow Rate, acfm 237,377.5 240,507.6 242,876.3 240,253.800

Percent Isokinetic of Sampling Rate, % 92.9 95.5 94.6 94.333

F-Factor, dscfm/MMBtu @ %O2 9688 9258 9305 9,417.000

Fw

Fc

Wednesday, July 06, 2011 Page 7 of 19
Emissions Testing Unit 1

Emissions Summary

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 3.73E-04 3.48E-04 4.83E-04 0.000

ppm 9.10E-01 8.44E-01 1.17E+00 0.975

ppm@7%O2 8.60E-01 8.02E-01 1.11E+00 0.924

Location: stack - Method 29

Compound: Antimony

Average

RunNumber 4 2 3

Mass_mg 0.328983 0.201963 0.402913 0.311

lb/mmBtuO2 5.66E-05 3.72E-05 7.19E-05 0.000

Compound: Arsenic

Average

RunNumber 4 2 3

Mass_mg 0.024403 0.021873 0.030363 0.026

lb/mmBtuO2 4.20E-06 4.03E-06 5.42E-06 0.000

Compound: Beryllium

Average

RunNumber 4 2 3

Mass_mg 0.00039 0.00036 0.00041 0.000

lb/mmBtuO2 6.71E-08 6.63E-08 7.31E-08 0.000

Compound: Cadmium

Average

RunNumber 4 2 3

Mass_mg 0.001653 0.001273 0.012 0.005

lb/mmBtuO2 2.84E-07 2.34E-07 2.14E-06 0.000

Compound: Chromium

Average

RunNumber 4 2 3

Mass_mg 0.01805 0.0253 0.021 0.021

lb/mmBtuO2 3.11E-06 4.66E-06 3.75E-06 0.000

Compound: Cobalt

Average

RunNumber 4 2 3

Wednesday, July 06, 2011 Page 8 of 19
Emissions Testing Unit 1

Mass_mg 0.121905 0.110901 0.12895 0.121

lb/mmBtuO2 2.10E-05 2.04E-05 2.30E-05 0.000

Compound: Lead

Average

RunNumber 4 2 3

Mass_mg 0.02426 0.01776 0.02061 0.021

lb/mmBtuO2 4.17E-06 3.27E-06 3.68E-06 0.000

Compound: Manganese

Average

RunNumber 4 2 3

Mass_mg 0.03513 0.0305 0.04324 0.036

lb/mmBtuO2 6.05E-06 5.62E-06 7.71E-06 0.000

Compound: Nickel

Average

RunNumber 4 2 3

Mass_mg 4.46186 3.67116 4.59296 4.242

lb/mmBtuO2 7.68E-04 6.76E-04 8.19E-04 0.001

Compound: Selenium

Average

RunNumber 4 2 3

Mass_mg 0.0184 0.0208 0.0187 0.019

lb/mmBtuO2 3.17E-06 3.83E-06 3.34E-06 0.000

Location: stack - Method 5

Compound: Filterable Particulate

Average

RunNumber 2 3 4

Mass_mg 353.4 467.6 469.5 430.167

lb/mmBtuO2 6.51E-02 8.34E-02 8.08E-02 0.076

Location: stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 1.47E+00 1.45E+00 1.45E+00 1.457

ppm 6.68E+02 6.59E+02 6.57E+02 661.333

ppm@7%O2 6.33E+02 6.24E+02 6.25E+02 627.333

Location: stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 4.89E-01 4.80E-01 4.78E-01 0.482

ppm 3.08E+02 3.04E+02 3.01E+02 304.333

ppm@7%O2 2.92E+02 2.88E+02 2.86E+02 288.667

Location: stack - OTM - 27/28

Wednesday, July 06, 2011 Page 9 of 19
Emissions Testing Unit 1

Compound: Filterable Particulate

Average

RunNumber 2 3 4

Mass_mg 110.8 157.4 145.3 137.833

lb/mmBtuO2 2.74E-02 3.57E-02 3.27E-02 0.032

Compound: Filterable PM2.5

Average

RunNumber 2 3 4

Mass_mg 90.2 132 144 122.067

lb/mmBtuO2 2.23E-02 2.99E-02 3.24E-02 0.028

Compound: Inorganic (Aqueous) Condensible P

Average

RunNumber 2 3 4

Mass_mg 212.5 162.3 128.4 167.733

lb/mmBtuO2 5.26E-02 3.68E-02 2.89E-02 0.039

Compound: Organic Condensible Particulate

Average

RunNumber 2 3 4

Mass_mg 113.5 172.8 83.2 123.167

lb/mmBtuO2 2.81E-02 3.92E-02 1.87E-02 0.029

Compound: Total Particulate

Average

RunNumber 2 3 4

Mass_mg 492.1 533.5 395.4 473.667

lb/mmBtuO2 1.22E-01 1.21E-01 8.90E-02 0.111

Compound: Total PM2.5

Average

RunNumber 2 3 4

Mass_mg 414.2 465.1 353.6 410.967

lb/mmBtuO2 1.02E-01 1.05E-01 7.96E-02 0.096

Wednesday, July 06, 2011 Page 10 of 19
Emissions Testing Unit 1

Process Run Data

Run Name Value UOM Comments

Target

Value

2 0

2 0

2 0

2 0

2 0

2 Residual Oil (No. 6) Burned 3452 1000 Gallons/hr 3086

2 0

2 Unit Gross Electric Generation 45.2 Mwe EPA Method 10 

and 25A: Run 4 

and Run 5

43

2 Unit Net Electric Generation 42.3 MWh EPA Method 

OTM 27/28: 

OTM27/28-3

40

2 Steam Output 389 1,000 lbs steam/hr EPA Method 5/29: 

M5/29-3

360

2 Average Heat Input 516 MMBtu/hr January 20, 2011 

Test Day

460

3 0

3 0

3 0

3 0

3 0

3 Residual Oil (No. 6) Burned 3205 1000 Gallons/hr 3086

3 0 EPA Method 3A, 

6C, and 7E: Run 

1, Run 2, and Run 

3

3 Unit Gross Electric Generation 44.4 Mwe EPA Method 10 

and 25A: Run 6

43

3 Unit Net Electric Generation 41.5 MWh EPA Method 

OTM 27/28: 

OTM27/28-4

40

3 Steam Output 388 1,000 lbs steam/hr EPA Method 5/29: 

M5/29-4

360

3 Average Heat Input 479 MMBtu/hr January 21, 2011 

Test Day

460

1 0

1 0

1 0

Wednesday, July 06, 2011 Page 11 of 19
Emissions Testing Unit 1

APCD Run Data

Process Lab Run Data

1 0

1 0

1 Residual Oil (No. 6) Burned 3166 1000 Gallons/hr 3086

1 0

1 Unit Gross Electric Generation 44.5 Mwe 43

1 Unit Net Electric Generation 41.6 MWh EPA Method 

OTM 27/28: 

OTM27/28-2

40

1 Steam Output 386 1,000 lbs steam/hr EPA Method 5/29: 

M5/29-2

360

1 Average Heat Input 473 MMBtu/hr January 19, 2011 

Test Day

460

Run Name Value UOM Comments

Target

Value

1 None 0

1 0

1 0

1 0

Run Name Value UOM Comments

1 none 0

1 0

1 0

1 0

1 0

Wednesday, July 06, 2011 Page 12 of 19
Emissions Testing Unit 1

Sampling / Stack Data Results Detail

Location stack - Method 10

Average

Run Number 1 2 3

Test Date 1/20/2011 1/20/2011 1/21/2011

Run Start Time 11:13:00 AM 1:48:00 PM 10:01:00 AM

Run Finish Time 1:13:00 PM 3:48:00 PM 12:01:00 PM

Carbon Dioxide, % 11.74 11.72 11.65 11.703

Oxygen, % 6.2 6.27 6.24 6.237

Fuel Factor 1.25 1.25 1.26

Dry Volumetric Flow Rate, dry scfm 136576 128782 137514 134,290.667

F-Factor, dscfm/MMBtu @ %O2 9258 9258 9305 9,273.667

Moisture, % 12.41 12.83 12.12 12.453

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 48 48 48 48.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0.13 -0.17 0.01 -0.010

Calibration Pre Zero Cylinder Bias 0.32 -0.95 0.21 -0.140

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID COCC149350-

Diluted2

COCC149350-

Diluted2

COCC116748-

Diluted2

Calibration Pre High Cylinder Instrument Response 9.16 9.48 9.35 9.330

Calibration Pre High Cylinder Bias -1.53 -0.16 -455.91 -152.533

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response -0.17 0.25 0.12 0.067

Calibration Post Zero Cylinder Bias -1.27 1.27 0.79 0.263

Calibration Post Zero Cylinder Drift 1.59 2.22 0.58 1.463

Calibration Post High Cylinder ID COCC149350-

Diluted2

COCC149350-

Diluted2

COCC116748-

Diluted2

Calibration Post High Cylinder Instrument Response 9.48 9.3 9.38 9.387

Calibration Post High Cylinder Bias 0.16 -1.11 -455.76 -152.237

Calibration Post High Cylinder Drift 1.69 0.95 0.1500000000

00034

0.930

Cavg -0.29 -0.06 -0.18 -0.177

Cavg Units ppmvd ppmvd ppmvd

Cgas 0 0 0 0.000

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc

Cgasw 0 0 0 0.000

Cgasw Units

Wednesday, July 06, 2011 Page 13 of 19
Emissions Testing Unit 1

Location stack - Method 25A

Average

Run Number 1 2 3

Test Date 1/20/2011 1/20/2011 1/21/2011

Run Start Time 11:13:00 AM 1:48:00 PM 10:01:00 AM

Run Finish Time 1:13:00 PM 3:48:00 PM 12:01:00 PM

Carbon Dioxide, % 11.74 11.72 11.65 11.703

Oxygen, % 6.2 6.27 6.24 6.237

Fuel Factor 1.25 1.25 1.26

Dry Volumetric Flow Rate, dry scfm 136576 128782 137514 134,290.667

F-Factor, dscfm/MMBtu @ %O2 9258 9258 9305 9,273.667

Moisture, % 12.41 12.83 12.12 12.453

Analyzer Make VIG VIG VIG

Analyzer Model 20 20 20 20.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response -0.01 0.08 0.04 0.037

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID THCCC74957-

Diluted1

THCCC74957-

Diluted1

THCCC74957-

Diluted1

Calibration Pre High Cylinder Instrument Response 2.47 2.42 2.57 2.487

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0.08 0.07 0.11 0.087

Calibration Post Zero Cylinder Bias 0.9 -0.12 0.84 0.540

Calibration Post Zero Cylinder Drift 0.9 0.12 0.84 0.620

Calibration Post High Cylinder ID THCCC74957-

Diluted1

THCCC74957-

Diluted1

THCCC74957-

Diluted1

Calibration Post High Cylinder Instrument Response 2.42 2.54 2.49 2.483

Calibration Post High Cylinder Bias -0.6 1.43 -0.95 -0.040

Calibration Post High Cylinder Drift 0.6 1.43 0.95 0.993

Cavg 0.8 0.78 1.08 0.887

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.9096 0.8441 1.1692 0.974

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc

Cgasw 0.7967427385

89212

0.735779625

779626

1.0275152749

4908

0.853

Cgasw Units ppmvw ppmvw ppmvw

Wednesday, July 06, 2011 Page 14 of 19
Emissions Testing Unit 1

Location stack - Method 29

Average

Run Number 2 3 4

Test Date 1/19/2011 1/20/2011 1/21/2011

Run Start Time 12:10:00 PM 12:18:00 PM 3:30:00 PM

Run Finish Time 4:27:00 PM 4:57:00 PM 7:46:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.261 0.26 0.261 0.261

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.02 1.02 1.020

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 1.70 1.66 1.75 1.703

Dry Gas Meter Volume Sampled, cubic feet 173.103 169.164 176.870 173.046

Average Dry Gas Meter Temperature, °F 104.69 99.71 100.60 101.667

Dry Gas Meter Volume Sampled, dscf 165.672 163.327 170.534 166.511

Total Moisture Liquid collected, g 492.2 510.3 514.1 505.533

Volume of Water Vapor, standard cubic feet 23.17 24.02 24.20 23.797

Moisture Content of Stack Gas, % 12.27 12.82 12.43 12.507

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8773 0.8718 0.8757 0.875

Carbon Dioxide, % 11.72 11.74 11.49 11.650

Oxygen, % 6.27 6.26 6.29 6.273

Carbon Monoxide & Nitrogen, % 82.01 82 82.22 82.077

Fuel Factor 1.25 1.25 1.27

Dry Molecular Weight, lb/lb-Mole 30.13 30.13 30.09 30.117

Wet Molecular weight, lb/lb-Mole 28.64 28.57 28.59 28.600

Flue Gas Static Pressure, inches of H2O 0.05 0.05 0.05 0.050

Absolute Flue Gas Pressure, inches of Mercury 29.90 29.90 29.90 29.900

Average Stack Gas Temperature, °F 354.17 357.71 358.17 356.683

Average Velocity Head, inches of H2O 0.5871343392

42741

0.593452660

603619

0.6297239915

08873

0.603

Average Stack Gas Velocity, feet/second 53.65 54.12 55.75 54.507

Stack Cross-Sectional Area, square feet 70.497 70.497 70.497 70.497

Dry Volumetric Flow Rate, dry scfm 129,023.3 128,777.7 133,174.8 130,325.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 226,929.8 228,917.9 235,812.5 230,553.400

Percent Isokinetic of Sampling Rate, % 101.5 101.0 101.2 101.233

Percent Excess Air, % 40.8 40.7 40.8 40.767

F-Factor, dscfm/MMBtu @ %O2 9688 9258 9305 9,417.000

Round Duct Diameter, inches 113.69 113.69 113.69

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Wednesday, July 06, 2011 Page 15 of 19
Emissions Testing Unit 1

Location stack - Method 5

Average

Run Number 2 3 4

Test Date 1/19/2011 1/20/2011 1/21/2011

Run Start Time 12:10:00 PM 12:18:00 PM 11:49:00 AM

Run Finish Time 4:27:00 PM 4:57:00 PM 7:46:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.261 0.26 0.261 0.261

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.02 1.02 1.020

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 1.70 1.66 1.75 1.703

Dry Gas Meter Volume Sampled, cubic feet 173.103 169.164 176.870 173.046

Average Dry Gas Meter Temperature, °F 104.69 99.71 100.60 101.667

Dry Gas Meter Volume Sampled, dscf 165.672 163.327 170.534 166.511

Total Moisture Liquid collected, g 492.2 510.3 514.1 505.533

Volume of Water Vapor, standard cubic feet 23.17 24.02 24.20 23.797

Moisture Content of Stack Gas, % 12.27 12.82 12.43 12.507

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8773 0.8718 0.8757 0.875

Carbon Dioxide, % 11.72 11.74 11.49 11.650

Oxygen, % 6.27 6.26 6.29 6.273

Carbon Monoxide & Nitrogen, % 82.01 82 82.22 82.077

Fuel Factor 1.25 1.25 1.27

Dry Molecular Weight, lb/lb-Mole 30.13 30.13 30.09 30.117

Wet Molecular weight, lb/lb-Mole 28.64 28.57 28.59 28.600

Flue Gas Static Pressure, inches of H2O 0.05 0.05 0.05 0.050

Absolute Flue Gas Pressure, inches of Mercury 29.90 29.90 29.90 29.900

Average Stack Gas Temperature, °F 354.17 357.71 358.17 356.683

Average Velocity Head, inches of H2O 0.5871343392

42741

0.593452660

603619

0.6297239915

08873

0.603

Average Stack Gas Velocity, feet/second 53.65 54.12 55.75 54.507

Stack Cross-Sectional Area, square feet 70.497 70.497 70.497 70.497

Dry Volumetric Flow Rate, dry scfm 129,023.3 128,777.7 133,174.8 130,325.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 226,929.8 228,917.9 235,812.5 230,553.400

Percent Isokinetic of Sampling Rate, % 101.5 101.0 101.2 101.233

Percent Excess Air, % 40.8 40.7 40.8 40.767

F-Factor, dscfm/MMBtu @ %O2 9688 9258 9305 9,417.000

Round Duct Diameter, inches 113.69 113.69 113.69

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Wednesday, July 06, 2011 Page 16 of 19
Emissions Testing Unit 1

Location stack - Method 6C

Average

Run Number 1 2 3

Test Date 1/21/2011 1/21/2011 1/21/2011

Run Start Time 10:01:00 AM 1:01:00 PM 3:47:00 PM

Run Finish Time 12:01:00 PM 3:01:00 PM 5:47:00 PM

Carbon Dioxide, % 11.65 11.69 11.65 11.663

Oxygen, % 6.24 6.22 6.28 6.247

Fuel Factor 1.26 1.26 1.25

Dry Volumetric Flow Rate, dry scfm 137514 137514 133190 136,072.667

F-Factor, dscfm/MMBtu @ %O2 9305 9305 9305 9,305.000

Moisture, % 12.12 12.12 12.43 12.223

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response -1 0 1 0.000

Calibration Pre Zero Cylinder Bias 0.11 0.17 0.33 0.203

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID SO2-

CC207182-

Diluted1

SO2-

CC207182-

Diluted1

SO2-

CC207182-

Diluted1

Calibration Pre High Cylinder Instrument Response 897.47 894.17 896.03 895.890

Calibration Pre High Cylinder Bias -1.16 -1.21 -0.79 -1.053

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0 1 0 0.333

Calibration Post Zero Cylinder Bias 0.22 0.28 0.22 0.240

Calibration Post Zero Cylinder Drift 0.11 0.11 0.11 0.110

Calibration Post High Cylinder ID SO2-

CC207182-

Diluted1

SO2-

CC207182-

Diluted1

SO2-

CC207182-

Diluted1

Calibration Post High Cylinder Instrument Response 894.17 896.03 893.67 894.623

Calibration Post High Cylinder Bias -1.52 -1.01 -1.05 -1.193

Calibration Post High Cylinder Drift 0.36 0.2 0.26 0.273

Cavg 661.19 652.73 650.11 654.677

Cavg Units ppmvd ppmvd ppmvd

Cgas 667.7287 659.4478 656.9824 661.386

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc

Cgasw 0 0 0 0.000

Cgasw Units

Wednesday, July 06, 2011 Page 17 of 19
Emissions Testing Unit 1

Location stack - Method 7E

Average

Run Number 1 2 3

Test Date 1/21/2011 1/21/2011 1/21/2011

Run Start Time 10:01:00 AM 1:01:00 PM 3:47:00 PM

Run Finish Time 12:01:00 PM 3:01:00 PM 5:47:00 PM

Carbon Dioxide, % 11.65 11.69 11.65 11.663

Oxygen, % 6.24 6.22 6.28 6.247

Fuel Factor 1.26 1.26 1.25

Dry Volumetric Flow Rate, dry scfm 137514 137514 133190 136,072.667

F-Factor, dscfm/MMBtu @ %O2 9305 9305 9305 9,305.000

Moisture, % 12.12 12.12 12.43 12.223

Analyzer Make CAI Model CAI Model

Analyzer Model 600 600 600.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 1 1 2 1.333

Calibration Pre Zero Cylinder Bias 0 0 0.11 0.037

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID NOxCC199835-

Diluted1

NOxCC199835-

Diluted1

NOxCC199835-

Diluted1

Calibration Pre High Cylinder Instrument Response 452 455 452.92 453.307

Calibration Pre High Cylinder Bias -0.78 -0.45 -0.68 -0.637

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 1 2 1 1.333

Calibration Post Zero Cylinder Bias 0 0.11 0 0.037

Calibration Post Zero Cylinder Drift 0 0.11 0.11 0.073

Calibration Post High Cylinder ID NOxCC199835-

Diluted1

NOxCC199835-

Diluted1

NOxCC199835-

Diluted1

Calibration Post High Cylinder Instrument Response 455 452.92 455.5 454.473

Calibration Post High Cylinder Bias -0.45 -0.68 -0.4 -0.510

Calibration Post High Cylinder Drift 0.33 0.23 0.28 0.280

Cavg 308.77 304.52 302.07 305.120

Cavg Units ppmvd ppmvd ppmvd

Cgas 308.4502 303.7165 301.0945 304.420

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc

Cgasw 0 0 0 0.000

Cgasw Units

Wednesday, July 06, 2011 Page 18 of 19
Emissions Testing Unit 1

Location stack - OTM - 27/28

Average

Run Number 2 3 4

Test Date 1/19/2011 1/20/2011 1/21/2011

Run Start Time 7:40:00 AM 7:31:00 AM 9:06:00 AM

Run Finish Time 2:17:00 PM 2:48:00 PM 3:37:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 364.7141317 368.2644781 371.5

Nozzle Diameter, inches 0.186 0.186 0.186 0.186

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.99 0.99 0.99 0.990

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 0.50 0.50 0.49 0.497

Dry Gas Meter Volume Sampled, cubic feet 130.696 135.406 137.200 134.434

Average Dry Gas Meter Temperature, °F 93.79 90.83 92.54 92.387

Dry Gas Meter Volume Sampled, dscf 123.433 128.568 129.865 127.289

Total Moisture Liquid collected, g 360.4 386.9 380.2 375.833

Volume of Water Vapor, standard cubic feet 16.96 18.21 17.90 17.690

Moisture Content of Stack Gas, % 12.08 12.41 12.11 12.200

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8792 0.8759 0.8789 0.878

Carbon Dioxide, % 11.76 11.74 11.67 11.723

Oxygen, % 6.28 6.26 6.23 6.257

Carbon Monoxide & Nitrogen, % 81.96 82 82.1 82.020

Fuel Factor 1.24 1.25 1.26

Dry Molecular Weight, lb/lb-Mole 30.13 30.13 30.12 30.127

Wet Molecular weight, lb/lb-Mole 28.66 28.62 28.65 28.643

Flue Gas Static Pressure, inches of H2O 0.05 0.05 0.05 0.050

Absolute Flue Gas Pressure, inches of Mercury 29.90 29.90 29.90 29.900

Average Stack Gas Temperature, °F 349.25 353.92 356.00 353.057

Average Velocity Head, inches of H2O 0.6466074894

8756

0.659257694

945986

0.6712826861

25964

0.659

Average Stack Gas Velocity, feet/second 56.12 56.86 57.42 56.800

Stack Cross-Sectional Area, square feet 70.497 70.497 70.497 70.497

Dry Volumetric Flow Rate, dry scfm 136,078.0 136,566.8 138,031.4 136,892.067

Actual Wet Volumetric Flue Gas Flow Rate, acfm 237,377.5 240,507.6 242,876.3 240,253.800

Percent Isokinetic of Sampling Rate, % 92.9 95.5 94.6 94.333

Percent Excess Air, % 40.9 40.7 40.3 40.633

F-Factor, dscfm/MMBtu @ %O2 9688 9258 9305 9,417.000

Round Duct Diameter, inches 113.69 113.69 113.69

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Wednesday, July 06, 2011 Page 19 of 19