Appendix B - Mercury Tracking Sheet for Boiler Data Review

Facility/Unit Fuel 

Category

Run #

Sample 

Time 

(min.)

Sample 

Volume 

(dscf)

Filter Temp, 

avg. (F)

Reported 

Value 

(lb/Mmbtu)

(W)

Hg - Filter 

(1B)

Hg - Probe 

Wash (2B)

Hg - Nitric 

(3A)

Hg - 

Permanganate 

(3B)

Hg - HCl 

Rinse (3C)

Count of 

Hg 

Fractions

SUM of Hg 

Fractions 

(ug)

(X)

Reported Hg 

Fraction Value 

(ug)

(Y)

% Difference 

between Reported 

and Review Values

(X-Y)/(X)

Calculated lb/mmBtu 

Based on Ratio of 

Measured Fractions

Z = (W*X/Y)

AKDoyonUtilities_AK #4 Solid 1 60 60.192 246 3.36E-07 0.03 0.5 0.01 0.05 0.05 5 0.64 0.64 0.00% 3.36E-07

AKDoyonUtilities_AK #4 Solid 2 60 61.418 247 4.12E-07 0.03 0.68 0.01 0.05 0.05 5 0.82 0.82 0.00% 4.12E-07

AKDoyonUtilities_AK #4 Solid 3 60 59.13 244 3.07E-07 0.03 0.44 0.01 0.05 0.05 5 0.58 0.58 0.00% 3.07E-07

GAGPSRMRiincon EU 002 Solid 1 120 60.459 241 8.14E-07 0.78 0.32 0.04 0.06 0.37 5 1.57 1.57 0.00% 8.14E-07

GAGPSRMRiincon EU 002 Solid 2 120 50.327 246 3.20E-07 0.01 0.17 0.01 0.02 0.31 5 0.52 0.51 1.92% 3.26E-07

IDAmalgamatedSugarCoTwinFalls - SB-1 Solid 1 120 78.341 251 2.41E-04 0.01 0.68 0.01 0.16 0.022 5 0.88 0.65 26.30% 3.27E-04

IDAmalgamatedSugarCoTwinFalls - SB-1 Solid 2 120 80.205 255 2.50E-04 0.01 0.84 0.01 0.04 0.022 5 0.92 0.73 20.61% 3.15E-04

IDAmalgamatedSugarCoTwinFalls - SB-1 Solid 3 120 77.571 246 2.76E-04 0.01 0.76 0.01 0.16 0.022 5 0.96 0.77 19.75% 3.44E-04

MITBSimonPowerPlant- Unit 1 (6/13/2007) Solid 1 120 78.628 252 7.28E-07 0.44 0.47 1.69 0.05 0.05 5 2.70 1.83 32.22% 1.07E-06

MITBSimonPowerPlant- Unit 1 (6/13/2007) Solid 2 120 76.747 251 2.36E-07 0.21 0.75 0.05 0.05 0.05 5 1.11 0.63 43.24% 4.16E-07

MITBSimonPowerPlant- Unit 1 (6/13/2007) Solid 3 120 74.277 249 1.22E-07 0.04 0.53 0.05 0.05 0.05 5 0.72 0.24 66.67% 3.66E-07

ALIPCourtland No. 3 Combination Boier / 11CU301 Solid 1 240 127 250 4.12E-07 0.15 0.084 0.017 0.034 1.05 5 1.34 1.10 17.60% 5.00E-07

ALIPCourtland No. 3 Combination Boier / 11CU301 Solid 2 240 125 249 5.22E-07 0.0066 0.0008 0.1938 0.261 1.03 5 1.49 1.29 13.55% 6.04E-07

ALIPCourtland No. 3 Combination Boier / 11CU301 Solid 3 240 119 246 3.08E-07 0.0063 0.21 0.0021 0.063 0.561 5 0.84 0.62 26.40% 4.18E-07

GASPNewsprint - PB2 Solid 1 240 163 253 1.17E-07 0.015 0.45 0.0051 0.025 0.03 5 0.53 0.53 0.02% 1.17E-07

GASPNewsprint - PB2 Solid 2 240 139 251 3.45E-07 0.015 0.5 0.005 0.22 0.583 5 1.32 1.32 0.00% 3.45E-07

GASPNewsprint - PB2 Solid 3 240 139 249 4.19E-07 0.015 0.51 0.0114 0.244 0.807 5 1.59 1.59 0.03% 4.19E-07

IAMonsantoMuscatine - Boiler #8 (EP-195) Solid 1 240 165.27 249 1.11E-07 0.04 0.056 0.325 0.001 0.111 5 0.53 0.53 0.00% 1.11E-07

IAMonsantoMuscatine - Boiler #8 (EP-195) Solid 2 240 169.796 251 3.28E-07 0.04 0.082 0.831 0.001 0.654 5 1.61 1.61 0.00% 3.28E-07

IAMonsantoMuscatine - Boiler #8 (EP-195) Solid 3 240 166.058 251 2.45E-07 0.04 0.064 0.972 0.055 0.063 5 1.19 1.19 0.00% 2.45E-07

IARoquetteAmerica - Circulating Fluidized Bed Boiler (121) Solid 1 192 150.658 249 5.92E-08 0.06 0.12 0.12 0.084 0.089 5 0.47 0.32 32.35% 8.75E-08

IARoquetteAmerica - Circulating Fluidized Bed Boiler (121) Solid 2 192 151.674 248 3.59E-08 0.06 0.12 0.14 0.11 0.086 5 0.52 0.20 61.24% 9.27E-08

IARoquetteAmerica - Circulating Fluidized Bed Boiler (121) Solid 3 192 148.593 242 7.61E-08 0.06 0.12 0.12 0.088 0.084 5 0.47 0.41 13.14% 8.76E-08

ILPolyOne - B1 Solid 1 240 172.203 No Data 1.08E-07 0.653 0.28 0.0072 0.025 0.017 5 0.98 0.77 21.20% 1.37E-07

ILPolyOne - B1 Solid 2 240 164.574 No Data 1.62E-07 0.017 0.8 No Data No Data No Data 2 0.82 0.66 18.73% 1.99E-07

ILPolyOne - B1 Solid 3 240 165.647 No Data 1.42E-07 0.015 0.3 No Data No Data No Data 2 0.32 0.30 4.76% 1.49E-07

MEFPLEnergyWyman Unit #5 Liquid 1 No Data No Data No Data No Data 0.015 0.4 0.0055 0.025 0.153 5 0.60 0.60 -0.25%

MEFPLEnergyWyman Unit #5 Liquid 2 No Data No Data No Data No Data 0.186 0.34 0.0062 0.025 0.165 5 0.72 0.72 0.30%

MEFPLEnergyWyman Unit #5 Liquid 3 No Data No Data No Data No Data 0.015 0.37 0.0058 0.025 0.104 5 0.52 0.52 -0.04%

MITBSimonPowerPlant - Unit 1 (2009) Solid 1 240 178.791 No Data 2.62E-07 0.056 Combined 1.71 0.025 Combined 3 1.79 1.60 10.66% 2.93E-07

MITBSimonPowerPlant - Unit 1 (2009) Solid 2 240 198.23 No Data 1.14E-07 0.136 Combined 0.8 0.025 Combined 3 0.96 0.77 19.88% 1.42E-07

MITBSimonPowerPlant - Unit 1 (2009) Solid 3 240 196.014 No Data 1.54E-07 0.347 Combined 0.87 0.025 Combined 3 1.24 1.05 15.46% 1.82E-07

NCDomtar 65-25-0310 (No. 2 Hog Fuel Boiler) Solid 1 240 161.884 248 1.68E-07 0.19 2.4 0.1 0.08 0.058 5 2.83 0.25 91.23% 1.92E-06

NCDomtar 65-25-0310 (No. 2 Hog Fuel Boiler) Solid 2 240 166.996 251 1.81E-07 0.24 0.54 0.1 0.08 0.049 5 1.01 0.83 17.84% 2.20E-07

NCDomtar 65-25-0310 (No. 2 Hog Fuel Boiler) Solid 3 240 157.615 255 1.85E-07 0.25 2.3 0.1 0.1 0.027 5 2.78 0.28 90.03% 1.85E-06

NCTysonHarmony - TYS-ES-21 Solid 1 120 77.941 246 2.70E-07 0.6 0.4 0.2 0.5 0.4 5 2.10 0.60 71.43% 9.45E-07

NCTysonHarmony - TYS-ES-21 Solid 2 120 74.864 248 2.50E-07 0.52 0.4 0.2 0.5 0.4 5 2.02 0.52 74.26% 9.71E-07

NCTysonHarmony - TYS-ES-21 Solid 3 120 82.735 251 2.10E-07 0.53 0.4 0.2 0.5 0.4 5 2.03 0.53 73.89% 8.04E-07

NJVinelandMuniElectric-HowardDown - Unit 9 Liquid 1 240 147.289 250 1.30E-07 0.1 0.6 0.2 0.5 0.714 5 2.11 0.71 66.27% 3.85E-07

NJVinelandMuniElectric-HowardDown - Unit 9 Liquid 2 240 149.988 251 2.60E-07 0.1 0.681 0.2 0.5 0.766 5 2.25 1.45 35.47% 4.03E-07

NJVinelandMuniElectric-HowardDown - Unit 9 Liquid 3 240 147.912 249 2.20E-07 0.1 0.804 0.2 0.5 0.403 5 2.01 1.21 39.71% 3.65E-07

PABoeingRidleyPark - 033 Liquid 1 240 150.708 251 1.29E-07 0.053 0.0051 0.38 0.025 0.295 5 0.76 0.76 0.00%

PABoeingRidleyPark - 033 Liquid 2 240 139.304 250 9.68E-08 0.015 0.356 0.0051 0.025 0.131 5 0.53 0.53 1.13% 9.79E-08

PABoeingRidleyPark - 033 Liquid 3 240 132.854 252 1.16E-07 0.015 0.336 0.0051 0.025 0.173 5 0.55 0.55 1.08% 1.17E-07

PANorfolkSouthern - 031 and 032 and 033 Solid 1 120 71.466 254 1.63E-04 0.6 No Data No Data 1.83 No Data 2 2.43 1.83 24.69% 2.16E-04

PANorfolkSouthern - 031 and 032 and 033 Solid 2 120 74.91 255 1.25E-04 0.6 No Data No Data 1.41 No Data 2 2.01 1.41 29.85% 1.78E-04

PANorfolkSouthern - 031 and 032 and 033 Solid 3 120 75.024 258 1.15E-04 0.6 No Data No Data 1.28 No Data 2 1.88 1.28 31.91% 1.69E-04

SCBowaterCoatedPaper - Combination Boiler No. 2 Solid 1 240 163.973 240 2.97E-07 0.015 0.234 0.0064 0.4 0.025 5 0.68 0.68 0.06% 2.97E-07

SCBowaterCoatedPaper - Combination Boiler No. 2 Solid 2 240 178.41 242 3.64E-07 0.016 0.453 0.0054 0.43 0.025 5 0.93 0.93 0.04% 3.64E-07

SCBowaterCoatedPaper - Combination Boiler No. 2 Solid 3 240 177.254 244 9.18E-07 0.043 1.24 0.006 0.36 0.025 5 1.67 1.87 -11.95% 8.20E-07

SCBowaterCoatedPaper - Combination Boiler No. 2 Solid 1 96 52.934 233 2.75E-07 0.086 0.44 No Data No Data 0.15 3 0.68 0.24 65.09% 7.88E-07

SCBowaterCoatedPaper - Combination Boiler No. 2 Solid 2 96 53.144 236 2.11E-07 0.074 0.43 No Data No Data 0.11 3 0.61 0.18 70.03% 7.04E-07

TNBowaterNewsprint - Bubbling Fluidized Bed Boiler Solid 1 60 41.8825 246 3.00E-07 0.1 0.91 0.04 0.1 0.32 5 1.47 0.91 38.10% 4.85E-07

TNBowaterNewsprint - Bubbling Fluidized Bed Boiler Solid 2 60 40.4945 248 4.00E-07 0.07 0.95 0.03 0.1 0.38 5 1.53 0.91 40.52% 6.73E-07

TNBowaterNewsprint - Bubbling Fluidized Bed Boiler Solid 3 60 38.888 251 3.00E-07 0.08 0.87 0.1 0.1 0.24 5 1.39 0.83 40.29% 5.02E-07

Hg fractions from Review
Appendix B - Mercury Tracking Sheet for Boiler Data Review

Facility/Unit Fuel 

Category

Run #

Sample 

Time 

(min.)

Sample 

Volume 

(dscf)

Filter Temp, 

avg. (F)

Reported 

Value 

(lb/Mmbtu)

(W)

Hg - Filter 

(1B)

Hg - Probe 

Wash (2B)

Hg - Nitric 

(3A)

Hg - 

Permanganate 

(3B)

Hg - HCl 

Rinse (3C)

Count of 

Hg 

Fractions

SUM of Hg 

Fractions 

(ug)

(X)

Reported Hg 

Fraction Value 

(ug)

(Y)

% Difference 

between Reported 

and Review Values

(X-Y)/(X)

Calculated lb/mmBtu 

Based on Ratio of 

Measured Fractions

Z = (W*X/Y)

Hg fractions from Review

TNNissanSmyrna - Boiler 2 Solid 1 60 40.79 258 8.00E-07 0.29 0.17 0.002 0.56 0.05 5 1.07 1.07 0.00% 8.00E-07

TNNissanSmyrna - Boiler 2 Solid 2 60 44.133 256 5.20E-07 0.29 0.06 0.01 0.36 0.05 5 0.77 0.77 0.00% 5.20E-07

TNNissanSmyrna - Boiler 2 Solid 3 60 42.609 255 3.20E-07 0.3 0.03 0.002 0.07 0.05 5 0.45 0.45 0.00% 3.20E-07

TNNissanSmyrna - Boiler 3 Solid 1 60 43.078 261 5.00E-07 0.33 0.09 0.08 0.05 0.21 5 0.76 0.76 0.00% 5.00E-07

TNNissanSmyrna - Boiler 3 Solid 2 60 44.819 260 3.00E-07 0.32 0.03 0.003 0.05 0.05 5 0.45 0.45 0.00% 3.00E-07

TNNissanSmyrna - Boiler 3 Solid 3 60 43.161 261 4.50E-07 0.31 0.06 0.032 0.05 0.21 5 0.66 0.66 0.00% 4.50E-07

VADukeEnergyNarrows Boiler #2 Solid 1 60 42.371 248 2.50E-06 0.1 1.6 0.2 0.5 0.4 5 2.80 1.60 42.86% 4.38E-06

VADukeEnergyNarrows Boiler #2 Solid 2 60 32.941 250 1.91E-06 0.1 1.17 0.2 0.5 0.4 5 2.37 1.17 50.63% 3.87E-06

VADukeEnergyNarrows Boiler #2 Solid 3 60 41.279 255 2.30E-06 0.1 1.65 0.2 0.5 0.4 5 2.85 1.66 41.75% 3.95E-06

VADukeEnergyNarrows Boiler #7 Solid 1 60 46.005 248 9.37E-07 0.1 1.22 0.2 0.5 0.4 5 2.42 1.22 49.59% 1.86E-06

VADukeEnergyNarrows Boiler #7 Solid 2 60 37.101 249 1.19E-06 0.13 1.13 0.2 0.5 0.4 5 2.36 1.26 46.61% 2.23E-06

VADukeEnergyNarrows Boiler #7 Solid 3 60 47.861 251 9.56E-07 0.1 1.32 0.2 0.5 0.4 5 2.52 1.31 48.02% 1.84E-06

VAUniversityofVirginia - 7103-1-01R Solid 1 240 176.38 255 3.69E-07 No Data 0.1 No Data 1.9 No Data 2 2.00 1.31 34.50% 5.63E-07

VAUniversityofVirginia - 7103-1-01R Solid 2 240 169.546 257 3.86E-07 No Data No Data No Data 1.9 No Data 1 1.90 1.31 31.05% 5.60E-07

VAUniversityofVirginia - 7103-1-01R Solid 3 240 177.945 252 3.77E-07 No Data 0.1 No Data 1.9 No Data 2 2.00 1.31 34.50% 5.76E-07

WIGPGreenBay2818 - Stk 10 - Fluidized Bed Boiler #9 - Aug 

2004 Solid 4 60 49.33 255 3.81E-06 No Data 0.1 3.29 0.87 No Data 3 4.26 4.16 2.35% 3.90E-06

WIGPGreenBay2818 - Stk 10 - Fluidized Bed Boiler #9 - Aug 

2004 Solid 5 60 48.566 251 3.90E-06 No Data 0.1 3.31 0.99 No Data 3 4.40 4.29 2.50% 4.00E-06

WIGPGreenBay2818 - Stk 10 - Fluidized Bed Boiler #9 - Aug 

2004 Solid 6 60 53.436 252 3.24E-06 No Data 0.1 2.85 0.62 No Data 3 3.57 3.48 2.52% 3.32E-06

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - 2005 Solid 4 60 41.043 248 3.55E-06 No Data 0.1 4.06 0.5 0.4 4 5.06 4.06 19.76% 4.42E-06

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - 2005 Solid 5 60 40.631 247 6.29E-06 No Data 2.42 4.71 0.5 0.4 4 8.03 7.13 11.21% 7.08E-06

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - 2005 Solid 6 60 41.2 246 6.92E-06 No Data 3.05 4.83 0.5 0.4 4 8.78 7.88 10.25% 7.71E-06

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - August 

2006 Solid 4 60 44.687 267 5.65E-06 No Data 0.1 4.74 0.5 0.56 4 5.90 5.29 10.34% 6.30E-06

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - August 

2006 Solid 5 60 46.809 264 2.90E-06 No Data 0.1 2.36 0.5 0.47 4 3.43 2.83 17.49% 3.51E-06

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - August 

2006 Solid 6 60 48.759 265 2.25E-06 No Data 0.1 2.51 0.5 0.4 4 3.51 2.51 28.49% 3.15E-06

GATempleInlandRome - WF Biomass 1 240 141.451 262 3.30E-07 0.52 0.126 0.054 0.08 0.89 5 1.67 1.68 -0.60% 3.28E-07

GATempleInlandRome - WF Biomass 2 240 148.796 262 4.20E-07 0.52 0.194 0.05 0.035 1.43 5 2.23 2.23 -0.04% 4.20E-07

GATempleInlandRome - WF Biomass 3 240 153.993 263 3.20E-07 0.5 0.113 0.05 0.025 1.05 5 1.74 1.74 -0.12% 3.20E-07

IAArchersDanielsMidlandDesMoines - Asea Boiler #1 Solid 1 240 218.31 250 6.30E-07 No Data No Data No Data No Data No Data 0

IAArchersDanielsMidlandDesMoines - Asea Boiler #1 Solid 2 240 214.84 251 6.10E-07 No Data No Data No Data No Data No Data 0

IAArchersDanielsMidlandDesMoines - Asea Boiler #1 Solid 3 240 217.37 250 1.00E-08 No Data No Data No Data No Data No Data 0

IAUofIowa - EP7 Boiler 11 Biomass 1 240 176.255 NR 3.09E-08 0.015 No Data 0.33 0.05 No Data 3 0.40 0.38 3.04% 3.19E-08

IAUofIowa - EP7 Boiler 11 Biomass 2 240 172.864 NR 3.22E-08 0.015 No Data 0.32 0.05 No Data 3 0.39 0.37 3.12% 3.32E-08

IAUofIowa - EP7 Boiler 11 Biomass 3 240 174.482 NR 3.06E-08 0.015 No Data 0.32 0.05 No Data 3 0.39 0.37 3.12% 3.16E-08

MNGPDuluth - EU33 Boiler #3 Liquid 1 180 15.87 249 9.66E-08 0.01 0.03 0.03 0.07 0.08 5 0.22 0.15 31.82% 1.42E-07

MNGPDuluth - EU33 Boiler #3 Liquid 2 180 148.38 242 4.31E-08 0.01 0.03 0.01 0.07 0.04 5 0.16 0.07 56.25% 9.85E-08

MNGPDuluth - EU33 Boiler #3 Liquid 3 180 144.35 248 3.59E-08 0.01 0.03 0.01 0.06 0.04 5 0.15 0.06 60.00% 8.98E-08

SCCogenSouth - B001 - Main Boiler Solid 1 120 91.6 248 ? 0.11 No Data 0.4 0.68 0.2 4 1.39 0.80 42.45%

SCCogenSouth - B001 - Main Boiler Solid 2 120 93.38 251 ? 0.04 No Data 0.4 0.53 0.2 4 1.17 0.57 51.28%

SCCogenSouth - B001 - Main Boiler Solid 3 120 87.44 255 ? 0.06 No Data 0.3 0.59 0.2 4 1.15 0.66 42.61%

SCCogenSouth - B001 - Main Boiler Solid 1 120 76.74 247 2.40E-07 0.1 0.56 0.5 0.2 4 1.36 0.60 55.88% 5.44E-07

SCCogenSouth - B001 - Main Boiler Solid 2 120 78.3 249 2.50E-07 0.1 0.66 0.5 0.2 4 1.46 0.60 58.90% 6.08E-07

SCCogenSouth - B001 - Main Boiler Solid 3 120 76.47 250 2.10E-07 0.1 0.63 0.5 0.2 4 1.43 0.50 65.03% 6.01E-07

SCCogenSouth - B001 - Main Boiler Solid 1 120 108.73 265 1.80E-06 0.2 2.4 0.2 1.1 1.5 5 5.40 2.60 51.85% 3.74E-06

SCCogenSouth - B001 - Main Boiler Solid 2 120 107.32 266 8.19E-07 0.2 2.6 0.3 0.6 1.9 5 5.60 2.50 55.36% 1.83E-06

SCCogenSouth - B001 - Main Boiler Solid 3 120 106.37 264 7.37E-07 0.2 2.7 0.2 2.1 1 5 6.20 2.10 66.13% 2.18E-06

SCCogenSouth - B001 - Main Boiler Solid 1 240 155.04 253 1.29E-07 0.1 0.2 1 0.5 0.4 5 2.20 0.60 72.73% 4.71E-07
Appendix B - Mercury Tracking Sheet for Boiler Data Review

Facility/Unit Fuel 

Category

Run #

Sample 

Time 

(min.)

Sample 

Volume 

(dscf)

Filter Temp, 

avg. (F)

Reported 

Value 

(lb/Mmbtu)

(W)

Hg - Filter 

(1B)

Hg - Probe 

Wash (2B)

Hg - Nitric 

(3A)

Hg - 

Permanganate 

(3B)

Hg - HCl 

Rinse (3C)

Count of 

Hg 

Fractions

SUM of Hg 

Fractions 

(ug)

(X)

Reported Hg 

Fraction Value 

(ug)

(Y)

% Difference 

between Reported 

and Review Values

(X-Y)/(X)

Calculated lb/mmBtu 

Based on Ratio of 

Measured Fractions

Z = (W*X/Y)

Hg fractions from Review

SCCogenSouth - B001 - Main Boiler Solid 2 240 154.94 251 1.13E-07 0.1 0.2 1 0.5 0.4 5 2.20 0.60 72.73% 4.16E-07

SCCogenSouth - B001 - Main Boiler Solid 3 240 158.45 254 2.50E-07 0.1 0.2 1 1.115 0.4 5 2.82 1.12 60.21% 6.28E-07

WVMountainStateCarbonFollansbee - S1 Process Gas 1 240 163.271 243 6.88E-06 0.023 3.89 ok 0.152 30.3 4 34.37 34.36 0.01% 6.88E-06

WVMountainStateCarbonFollansbee - S1 Process Gas 2 240 124.385 251 5.82E-06 0.051 4.23 ok 0.14 24.1 4 28.52 28.52 0.00% 5.82E-06

WVMountainStateCarbonFollansbee - S1 Process Gas 3 240 143.477 251 5.91E-06 0.015 2.75 ok 0.194 25.5 4 28.46 28.46 0.01% 5.91E-06

NCDomtar - 65-25-0310 (No. 2 Hog Fuel Boiler) 1 120 74.893 237 2.01E-06 0.4 2 0.2 0.4 1.2 5 4.20 4.20 0.00% 2.01E-06

NCDomtar - 65-25-0310 (No. 2 Hog Fuel Boiler) 2 120 78.324 238 1.87E-06 0.4 2.2 0.2 0.4 1.1 5 4.30 4.30 0.00% 1.87E-06

NCDomtar - 65-25-0310 (No. 2 Hog Fuel Boiler) 3 120 77.557 237 1.97E-06 0.4 2 0.2 0.4 1.2 5 4.20 4.20 0.00% 1.97E-06

TNCargillMemphis - Stoker Boiler 8001 1 240 169.383 257 4.10E-07 0.2 1.3 0.4 0.16 0.28 5 2.34 1.63 30.34% 5.89E-07

TNCargillMemphis - Stoker Boiler 8001 2 240 172.476 257 2.70E-07 0.2 0.86 0.4 0.18 0.28 5 1.92 1.14 40.63% 4.55E-07

TNCargillMemphis - Stoker Boiler 8001 3 240 158.663 260 2.10E-07 0.2 0.73 0.4 0.16 0.28 5 1.77 0.81 54.24% 4.59E-07

VADukeEnergyNarrows - Boiler #1 1 60 37.837 258 6.17E-07 0.1 0.4 0.2 0.5 0.4 5 1.60 0.50 68.75% 1.97E-06

VADukeEnergyNarrows - Boiler #1 3 60 38.994 261 2.78E-07 0.228 0.4 0.2 0.5 0.4 5 1.73 0.23 86.69% 2.09E-06

VADukeEnergyNarrows - Boiler #1 4 60 38.585 266 2.54E-07 0.198 0.4 0.2 0.5 0.4 5 1.70 0.20 88.22% 2.16E-06

VADukeEnergyNarrows - Boiler #1 1 60 54.38 251 5.07E-06 0.1 3.98 0.41 0.5 0.4 5 5.39 4.39 18.55% 6.22E-06

VADukeEnergyNarrows - Boiler #1 2 60 51.201 252 4.22E-06 0.1 2.94 0.2 0.5 0.4 5 4.14 2.93 29.23% 5.96E-06

VADukeEnergyNarrows - Boiler #1 3 60 55.212 253 4.02E-06 0.1 2.95 0.2 0.5 0.4 5 4.15 2.95 28.92% 5.66E-06

VADukeEnergyNarrows - Boiler #7 1 60 59.38 235 7.25E-07 0.1 0.97 0.2 0.5 0.4 5 2.17 0.97 55.30% 1.62E-06

VADukeEnergyNarrows - Boiler #7 2 60 41.135 236 5.99E-07 0.1 0.61 0.2 0.5 0.4 5 1.81 0.61 66.30% 1.78E-06

VADukeEnergyNarrows - Boiler #7 3 60 43.425 241 6.90E-07 0.1 0.8 0.2 0.5 0.4 5 2.00 0.80 60.00% 1.73E-06

FLRayonierPerformance Condition 1 1 120 78 No Data 2.39E-07 0.412 0.11 0.005 0.41 0.1 5 1.04 0.52 49.86% 4.77E-07

FLRayonierPerformance Condition 1 2 120 74 No Data 2.11E-07 0.346 0.11 0.006 0.44 0.05 5 0.95 0.16 83.19% 1.26E-06

FLRayonierPerformance Condition 1 3 120 66 No Data 1.50E-07 0.333 0.05 0.005 0.42 0.05 5 0.86 0.33 61.54% 3.90E-07

FLRayonierPerformance Condition 2 1 120 74 No Data 3.48E-07 0.669 0.06 0.003 0.44 0.15 5 1.32 0.88 33.43% 5.23E-07

FLRayonierPerformance Condition 2 2 120 73 No Data 3.15E-07 0.7 0.06 0.006 0.45 0.05 5 1.27 0.73 42.34% 5.46E-07

FLRayonierPerformance Condition 2 3 120 71 No Data 1.89E-07 0.639 0.05 0.004 0.38 0.1 5 1.17 0.34 71.01% 6.52E-07

FLRayonierPerformance Condition 3 1 120 73 No Data 2.13E-07 0.503 0.05 0.002 0.35 0.05 5 0.96 0.50 47.64% 4.07E-07

FLRayonierPerformance Condition 3 2 120 69 No Data 1.86E-07 0.389 0.05 0.004 0.35 0.05 5 0.84 0.45 46.62% 3.48E-07

FLRayonierPerformance Condition 3 3 120 71 No Data 3.61E-07 0.772 0.09 0.005 0.45 0.05 5 1.37 0.86 37.09% 5.74E-07

MINeenahPaperMI Boiler 1- 7/25/2006 Solid 1 60 37.18 No Data 4.30E-07 No Data No Data No Data No Data No Data 0 0.00 0.54 #DIV/0! 0.00E+00

MINeenahPaperMI Boiler 1- 7/25/2006 Solid 2 60 37.95 No Data 4.20E-07 No Data No Data No Data No Data No Data 0 0.00 0.52 #DIV/0! 0.00E+00

MINeenahPaperMI Boiler 1- 7/25/2006 Solid 3 60 38.35 No Data 3.90E-07 No Data No Data No Data No Data No Data 0 0.00 0.43 #DIV/0! 0.00E+00

MINeenahPaperMI Boiler 1 - 8/1/2006 Solid 1 60 38.21 No Data 1.20E-07 No Data No Data No Data No Data No Data 0 0.00 1.40 #DIV/0! 0.00E+00

MINeenahPaperMI Boiler 1 - 8/1/2006 Solid 2 60 38.68 No Data 8.00E-08 No Data No Data No Data No Data No Data 0 0.00 1.00 #DIV/0! 0.00E+00

MINeenahPaperMI Boiler 1 - 8/1/2006 Solid 3 60 36.49 No Data 1.10E-07 No Data No Data No Data No Data No Data 0 0.00 1.20 #DIV/0! 0.00E+00

MNDESPHansONyman EU-07 - 3/6/2007 Solid 1 60 45.26 255 5.20E-07 No Data No Data No Data No Data No Data 0 0.00 0.68 #DIV/0! 0.00E+00

MNDESPHansONyman EU-07 - 3/6/2007 Solid 2 60 45.56 258 7.30E-07 No Data No Data No Data No Data No Data 0 0.00 0.86 #DIV/0! 0.00E+00

MNDESPHansONyman EU-07 - 3/6/2007 Solid 3 60 43.27 256 7.00E-07 No Data No Data No Data No Data No Data 0 0.00 0.86 #DIV/0! 0.00E+00

INPurdueUniverisity - Boiler 5 - 7/21/2009 Solid 1 240 210.648 No Data 1.15E-07 No Data No Data No Data No Data No Data 0 0.00 0.90 #DIV/0! 0.00E+00

INPurdueUniverisity - Boiler 5 - 7/21/2009 Solid 2 240 210.413 No Data 1.35E-07 No Data No Data No Data No Data No Data 0 0.00 1.01 #DIV/0! 0.00E+00

INPurdueUniverisity - Boiler 5 - 7/21/2009 Solid 3 240 201.621 No Data 1.18E-07 No Data No Data No Data No Data No Data 0 0.00 0.87 #DIV/0! 0.00E+00

NCGPRoxboro - ES-1 Wood fired Boiler - 7/14/2004 Solid 1 120 64.01 249 3.23E-07 No Data No Data No Data No Data No Data 0 0.00 0.49 #DIV/0! 0.00E+00

NCGPRoxboro - ES-1 Wood fired Boiler - 7/14/2004 Solid 2 120 71.68 251 2.43E-07 No Data No Data No Data No Data No Data 0 0.00 0.40 #DIV/0! 0.00E+00

NCGPRoxboro - ES-1 Wood fired Boiler - 7/14/2004 Solid 3 120 67.67 253 2.36E-07 No Data No Data No Data No Data No Data 0 0.00 0.36 #DIV/0! 0.00E+00

OHAppletonIdeas - Boiler 4 (B003) - 1/31/2003 Solid 1 120 95.988 245 3.37E-07 No Data No Data No Data No Data No Data 0 0.00 0.80 #DIV/0! 0.00E+00

OHAppletonIdeas - Boiler 4 (B003) - 1/31/2003 Solid 2 120 101.22 247 4.03E-07 No Data No Data No Data No Data No Data 0 0.00 0.90 #DIV/0! 0.00E+00

OHAppletonIdeas - Boiler 4 (B003) - 1/31/2003 Solid 3 120 96.171 244 4.13E-07 No Data No Data No Data No Data No Data 0 0.00 0.90 #DIV/0! 0.00E+00

OKGPMuskogeeMill B-3 - 5/20/2003 Solid 1 120 73.815 243 4.00E-07 No Data No Data No Data No Data No Data 0 0.00 No Data #VALUE! #VALUE!

OKGPMuskogeeMill B-3 - 5/20/2003 Solid 2 120 73.411 241 4.00E-07 No Data No Data No Data No Data No Data 0 0.00 No Data #VALUE! #VALUE!

OKGPMuskogeeMill B-3 - 5/20/2003 Solid 3 120 77.913 258 6.00E-07 No Data No Data No Data No Data No Data 0 0.00 No Data #VALUE! #VALUE!

WIGPGreenBay2818 - B29 - Fluidized Bed Boiler #9 - 1992 - 

10/27/1992 Solid 1 120 90.73 255 2.04E-06 No Data No Data No Data 0.5 No Data 1 0.50 No Data #VALUE! #VALUE!

WIGPGreenBay2818 - B29 - Fluidized Bed Boiler #9 - 1992 - 

10/27/1992 Solid 2 120 92.18 257 2.82E-06 No Data No Data No Data No Data No Data 0 0.00 No Data #VALUE! #VALUE!

WIGPGreenBay2818 - B29 - Fluidized Bed Boiler #9 - 1992 - 

10/27/1992 Solid 3 120 100.79 255 7.83E-06 No Data No Data No Data No Data No Data 0 0.00 No Data #VALUE! #VALUE!
Appendix B - Mercury Tracking Sheet for Boiler Data Review

Facility/Unit

AKDoyonUtilities_AK #4

AKDoyonUtilities_AK #4

AKDoyonUtilities_AK #4

GAGPSRMRiincon EU 002

GAGPSRMRiincon EU 002

IDAmalgamatedSugarCoTwinFalls - SB-1

IDAmalgamatedSugarCoTwinFalls - SB-1

IDAmalgamatedSugarCoTwinFalls - SB-1

MITBSimonPowerPlant- Unit 1 (6/13/2007)

MITBSimonPowerPlant- Unit 1 (6/13/2007)

MITBSimonPowerPlant- Unit 1 (6/13/2007)

ALIPCourtland No. 3 Combination Boier / 11CU301

ALIPCourtland No. 3 Combination Boier / 11CU301

ALIPCourtland No. 3 Combination Boier / 11CU301

GASPNewsprint - PB2

GASPNewsprint - PB2

GASPNewsprint - PB2

IAMonsantoMuscatine - Boiler #8 (EP-195)

IAMonsantoMuscatine - Boiler #8 (EP-195)

IAMonsantoMuscatine - Boiler #8 (EP-195)

IARoquetteAmerica - Circulating Fluidized Bed Boiler (121)

IARoquetteAmerica - Circulating Fluidized Bed Boiler (121)

IARoquetteAmerica - Circulating Fluidized Bed Boiler (121)

ILPolyOne - B1

ILPolyOne - B1

ILPolyOne - B1

MEFPLEnergyWyman Unit #5

MEFPLEnergyWyman Unit #5

MEFPLEnergyWyman Unit #5

MITBSimonPowerPlant - Unit 1 (2009)

MITBSimonPowerPlant - Unit 1 (2009)

MITBSimonPowerPlant - Unit 1 (2009)

NCDomtar 65-25-0310 (No. 2 Hog Fuel Boiler)

NCDomtar 65-25-0310 (No. 2 Hog Fuel Boiler)

NCDomtar 65-25-0310 (No. 2 Hog Fuel Boiler)

NCTysonHarmony - TYS-ES-21

NCTysonHarmony - TYS-ES-21

NCTysonHarmony - TYS-ES-21

NJVinelandMuniElectric-HowardDown - Unit 9

NJVinelandMuniElectric-HowardDown - Unit 9

NJVinelandMuniElectric-HowardDown - Unit 9

PABoeingRidleyPark - 033

PABoeingRidleyPark - 033

PABoeingRidleyPark - 033

PANorfolkSouthern - 031 and 032 and 033

PANorfolkSouthern - 031 and 032 and 033

PANorfolkSouthern - 031 and 032 and 033

SCBowaterCoatedPaper - Combination Boiler No. 2

SCBowaterCoatedPaper - Combination Boiler No. 2

SCBowaterCoatedPaper - Combination Boiler No. 2

SCBowaterCoatedPaper - Combination Boiler No. 2

SCBowaterCoatedPaper - Combination Boiler No. 2

TNBowaterNewsprint - Bubbling Fluidized Bed Boiler

TNBowaterNewsprint - Bubbling Fluidized Bed Boiler

TNBowaterNewsprint - Bubbling Fluidized Bed Boiler

Hg - Filter 

(1B)

Hg - Probe 

Wash (2B)

Hg - Nitric 

(3A)

Hg - 

Permanganate 

(3B)

Hg - HCl 

Rinse (3C) Notes ACTION

Pre-Corrected 

Hg Value 

(lb/mmBtu)

0.03 0.42 0.01 0.05 0.05 Do not change

0.03 0.42 0.01 0.05 0.05 Do not change

0.03 0.42 0.01 0.05 0.05 Do not change

0.01 0.3 0.01 0.05 0.05 Do not change

0.01 0.3 0.01 0.05 0.05 Updated value to calculated lb/mmBtu value, Z

0.01 0.01 0.04 0.04 0.022

Blank subtraction was 22.7% of sample catch. Did not use DL as sample 

weight when result less than DL. (bias 2% low) Do not change, facility submitted corrections 2.56E-07

0.01 0.01 0.04 0.04 0.022

Blank subtraction was 22.7% of sample catch. Did not use DL as sample 

weight when result less than DL. (bias 2% low) Do not change, facility submitted corrections 2.80E-07

0.01 0.01 0.04 0.04 0.022

Blank subtraction was 22.7% of sample catch. Did not use DL as sample 

weight when result less than DL. (bias 2% low) Do not change, facility submitted corrections 2.92E-07

0.05 0.05 0.05 0.05 0.05 30% blank subtraction Updated value to calculated lb/mmBtu value, Z

0.05 0.05 0.05 0.05 0.05 35% blank subtraction Updated value to calculated lb/mmBtu value, Z

0.05 0.05 0.05 0.05 0.05 58% blank subtraction Updated value to calculated lb/mmBtu value, Z

0.015 0.005 0.025 0.025 0.025 Updated value to calculated lb/mmBtu value, Z

0.0066 0.008 0.025 0.025 0.025 Updated value to calculated lb/mmBtu value, Z

0.0063 0.0021 0.025 0.025 0.025 Updated value to calculated lb/mmBtu value, Z

0.015 0.45 0.0051 0.025 0.025 Do not change

0.015 0.49 0.0051 0.05 0.025 Do not change

0.015 0.51 0.0049 0.025 0.025 Do not change

0.004 0.03 0.03 0.001 0.003 Do not change

0.004 0.03 0.03 0.001 0.003 Do not change

0.004 0.03 0.03 0.001 0.003 Do not change

0.06 0.12 0.12 0.038 0.089 Data reported without considering BDL data Updated value to calculated lb/mmBtu value, Z

0.06 0.12 0.14 0.041 0.086 Data reported without considering BDL data Updated value to calculated lb/mmBtu value, Z

0.06 0.12 0.12 0.043 0.084 Data reported without considering BDL data Updated value to calculated lb/mmBtu value, Z

0.15 0.015 0.043 No Data No Data 17% blank subtraction - Used Hg fractions reported in ERT to update value Updated value to calculated lb/mmBtu value, Z

0.15 0.015 0.043 No Data No Data 18% blank subtraction - Used Hg fractions reported in ERT to update value Updated value to calculated lb/mmBtu value, Z

0.15 0.015 0.043 No Data No Data

Non detect on third run, reported as less than MDL (0.3) - Used Hg fractions 

reported in ERT to update value Updated value to calculated lb/mmBtu value, Z

0.015 0.34 0.0055 0.025 0.025

All lab data present, but no test report. No way to confirm volume or mass 

emissions rate Do not change, data verified through ERT

0.015 0.34 0.0062 0.025 0.025

All lab data present, but no test report. No way to confirm volume or mass 

emissions rate Do not change, data verified through ERT

0.015 0.37 0.0058 0.025 0.025

All lab data present, but no test report. No way to confirm volume or mass 

emissions rate Do not change, data verified through ERT

0.015 0.15 No Data 0.025 No Data No field data sheets to validate q/a. Do not change, facility submitted corrections 2.70E-07

0.015 0.15 No Data 0.025 No Data No field data sheets to validate q/a. Do not change, facility submitted corrections 1.22E-07

0.015 0.15 No Data 0.025 No Data No field data sheets to validate q/a. Do not change, facility submitted corrections 1.61E-07

0.03 2.4 0.1 0.08 0.1

Report does not contain enough information to determine how blank 

subtraction was handled. MDL values for Nitric/Peroxide are very high. Updated value to calculated lb/mmBtu value, Z

0.03 2.2 0.1 0.08 0.1

Report does not contain enough information to determine how blank 

subtraction was handled. MDL values for Nitric/Peroxide are very high. Updated value to calculated lb/mmBtu value, Z

0.03 2.3 0.1 0.1 0.1

Report does not contain enough information to determine how blank 

subtraction was handled. MDL values for Nitric/Peroxide are very high. Updated value to calculated lb/mmBtu value, Z

0.4 0.4 0.2 0.5 0.4 High detection limit, 70% blank subtraction Updated value to calculated lb/mmBtu value, Z

0.4 0.4 0.2 0.5 0.4 High detection limit, 70% blank subtraction Updated value to calculated lb/mmBtu value, Z

0.4 0.4 0.2 0.5 0.4 High detection limit, 70% blank subtraction Updated value to calculated lb/mmBtu value, Z

0.1 0.6 0.2 0.5 0.2

High detection limits, blank subtraction % high. Half of field data sheets 

missing from report Updated value to calculated lb/mmBtu value, Z

0.1 0.6 0.2 0.5 0.2

High detection limits, blank subtraction % high. Half of field data sheets 

missing from report Updated value to calculated lb/mmBtu value, Z

0.1 0.6 0.2 0.5 0.2

High detection limits, blank subtraction % high. Half of field data sheets 

missing from report Updated value to calculated lb/mmBtu value, Z

0.015 0.15 0.005 0.013 0.013 Do not change

0.015 0.15 0.005 0.013 0.013 Updated value to calculated lb/mmBtu value, Z

0.015 0.15 0.005 0.013 0.013 Updated value to calculated lb/mmBtu value, Z

No Data No Data 0.22 1 1 Five Hg fractions not available Remove test data from floor calculations

No Data No Data No Data No Data No Data Five Hg fractions not available Remove test data from floor calculations

No Data No Data No Data No Data No Data Five Hg fractions not available Remove test data from floor calculations

0.015 0.025 0.0052 0.4 0.025 Do not change

0.015 0.025 0.0054 0.43 0.025 Do not change

0.015 0.025 0.0049 0.36 0.025 Run appears to be reported 11% high. Updated value to calculated lb/mmBtu value, Z

No Data 0.3 No Data No Data No Data 65 % blank reduction - only 2 runs Remove test data from floor calculations

No Data 0.3 No Data No Data No Data 70% blank reduction - only 2 runs. Remove test data from floor calculations

0.03 0.9 0.02 0.1 0.1 Updated value to calculated lb/mmBtu value, Z

0.03 0.9 0.02 0.1 0.1 Updated value to calculated lb/mmBtu value, Z

0.03 0.9 0.02 0.1 0.1 Updated value to calculated lb/mmBtu value, Z

Reported Detection limits (ug)
Appendix B - Mercury Tracking Sheet for Boiler Data Review

Facility/Unit

TNNissanSmyrna - Boiler 2

TNNissanSmyrna - Boiler 2

TNNissanSmyrna - Boiler 2

TNNissanSmyrna - Boiler 3

TNNissanSmyrna - Boiler 3

TNNissanSmyrna - Boiler 3

VADukeEnergyNarrows Boiler #2

VADukeEnergyNarrows Boiler #2

VADukeEnergyNarrows Boiler #2

VADukeEnergyNarrows Boiler #7

VADukeEnergyNarrows Boiler #7

VADukeEnergyNarrows Boiler #7

VAUniversityofVirginia - 7103-1-01R

VAUniversityofVirginia - 7103-1-01R

VAUniversityofVirginia - 7103-1-01R

WIGPGreenBay2818 - Stk 10 - Fluidized Bed Boiler #9 - Aug 

2004

WIGPGreenBay2818 - Stk 10 - Fluidized Bed Boiler #9 - Aug 

2004

WIGPGreenBay2818 - Stk 10 - Fluidized Bed Boiler #9 - Aug 

2004

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - 2005

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - 2005

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - 2005

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - August 

2006

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - August 

2006

WIGPGreenBay2818 - Stack 10 - Fluidized Bed Boiler #9 - August 

2006

GATempleInlandRome - WF

GATempleInlandRome - WF

GATempleInlandRome - WF

IAArchersDanielsMidlandDesMoines - Asea Boiler #1

IAArchersDanielsMidlandDesMoines - Asea Boiler #1

IAArchersDanielsMidlandDesMoines - Asea Boiler #1

IAUofIowa - EP7 Boiler 11

IAUofIowa - EP7 Boiler 11

IAUofIowa - EP7 Boiler 11

MNGPDuluth - EU33 Boiler #3

MNGPDuluth - EU33 Boiler #3

MNGPDuluth - EU33 Boiler #3

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

Hg - Filter 

(1B)

Hg - Probe 

Wash (2B)

Hg - Nitric 

(3A)

Hg - 

Permanganate 

(3B)

Hg - HCl 

Rinse (3C) Notes ACTION

Pre-Corrected 

Hg Value 

(lb/mmBtu)

Reported Detection limits (ug)

0.03 0.29 0.002 0.05 0.05 Do not change

0.03 0.29 0.002 0.05 0.05 Do not change

0.03 0.3 0.002 0.05 0.05 Do not change

0.03 0.33 0.004 0.05 0.05 Do not change

0.03 0.32 0.002 0.05 0.05 Do not change

0.03 0.31 0.003 0.05 0.05 Do not change

0.1 No Data 0.2 0.5 0.4 DL data not reported. Updated value to calculated lb/mmBtu value, Z

0.1 No Data 0.2 0.5 0.4 DL data not reported. Updated value to calculated lb/mmBtu value, Z

0.1 No Data 0.2 0.5 0.4 DL data not reported. Updated value to calculated lb/mmBtu value, Z

0.1 No Data 0.2 0.5 0.4 DL data not reported. Updated value to calculated lb/mmBtu value, Z

0.1 No Data 0.2 0.5 0.4 DL data not reported. Updated value to calculated lb/mmBtu value, Z

0.1 No Data 0.2 0.5 0.4 DL data not reported. Updated value to calculated lb/mmBtu value, Z

No Data No Data No Data No Data No Data

Scant metals data from lab. Front and back half, no way to tell how blanks 

were treated. Do not change, data verified through ERT

No Data No Data No Data No Data No Data

Scant metals data from lab. Front and back half, no way to tell how blanks 

were treated. Do not change, data verified through ERT

No Data No Data No Data No Data No Data

Scant metals data from lab. Front and back half, no way to tell how blanks 

were treated. Do not change, data verified through ERT

No Data 0.1 0.3 0.5 No Data

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

No Data 0.1 0.3 0.5 No Data

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

No Data 0.1 0.3 0.5 No Data

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

? 0.1 0.3 0.5 0.4

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

? 0.1 0.3 0.5 0.4

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

? 0.1 0.3 0.5 0.4

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

? 0.1 0.5 0.5 0.4

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

? 0.1 0.5 0.5 0.4

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

? 0.1 0.5 0.5 0.4

Five Hg fractions not reported - 1 reported number for "front half" so it is not 

clear that both probe rinse and filter were combined or if one was not 

analyzed. Remove test data from floor calculations

0.52 0.015 0.045 0.05 0.025 Do not change

0.052 0.015 0.045 0.025 0.025 Do not change

0.05 0.015 0.05 0.025 0.025 Do not change

No Data No Data No Data No Data No Data

Lab results in concentration (mg/L) with no correlation to volume submitted. 

Data presented as <DL Do not change, facility submitted corrections 3.18E-08

No Data No Data No Data No Data No Data

Lab results in concentration (mg/L) with no correlation to volume submitted. 

Data presented as <DL Do not change, facility submitted corrections 2.80E-08

No Data No Data No Data No Data No Data

Run 3 very low, sixteen times less than R1 and R2, yet had detection ABOVE 

R1 and R2. Do not change, facility submitted corrections 5.53E-08

0.015 0.33 No Data 0.025 0.013 Five Hg fractions not available Remove test data from floor calculations

0.015 0.32 No Data 0.025 0.013 Five Hg fractions not available Remove test data from floor calculations

0.015 0.32 No Data 0.025 0.013 Five Hg fractions not available Remove test data from floor calculations

0.01 0.03 0.01 0.04 0.04 Reported ND as zero. Do not change, NCASI submitted corrections 1.28E-07

0.01 0.03 0.01 0.04 0.04 Reported ND as zero. Do not change, NCASI submitted corrections 9.77E-08

0.01 0.03 0.01 0.04 0.04 Reported ND as zero. Do not change, NCASI submitted corrections 8.91E-08

No Data No Data 0.4 No Data 0.2 Reported ND as zero. Do not change, NCASI submitted corrections 4.56E-07

No Data No Data 0.4 No Data 0.2 Reported ND as zero. Do not change, NCASI submitted corrections 3.75E-07

No Data No Data 0.4 No Data 0.2 Reported ND as zero. Do not change, NCASI submitted corrections 3.97E-07

No Data 0.1 0.56 0.5 0.2 Reported ND as zero. Do not change, NCASI submitted corrections 5.55E-07

No Data 0.1 0.66 0.5 0.2 Reported ND as zero. Do not change, NCASI submitted corrections 6.05E-07

No Data 0.1 0.63 0.5 0.2 Reported ND as zero. Do not change, NCASI submitted corrections 5.98E-07

0.2 0.7 0.4 0.1 1 Reported ND as zero. Do not change, NCASI submitted corrections 1.62E-06

0.2 0.7 0.4 0.1 1 Reported ND as zero. Do not change, NCASI submitted corrections 1.78E-06

0.2 0.7 0.4 0.1 1 Reported ND as zero. Do not change, NCASI submitted corrections 1.87E-06

0.1 0.2 1.52 0.5 0.4 Reported ND as zero. Do not change, NCASI submitted corrections 4.60E-07
Appendix B - Mercury Tracking Sheet for Boiler Data Review

Facility/Unit

SCCogenSouth - B001 - Main Boiler

SCCogenSouth - B001 - Main Boiler

WVMountainStateCarbonFollansbee - S1

WVMountainStateCarbonFollansbee - S1

WVMountainStateCarbonFollansbee - S1

NCDomtar - 65-25-0310 (No. 2 Hog Fuel Boiler)

NCDomtar - 65-25-0310 (No. 2 Hog Fuel Boiler)

NCDomtar - 65-25-0310 (No. 2 Hog Fuel Boiler)

TNCargillMemphis - Stoker Boiler 8001

TNCargillMemphis - Stoker Boiler 8001

TNCargillMemphis - Stoker Boiler 8001

VADukeEnergyNarrows - Boiler #1

VADukeEnergyNarrows - Boiler #1

VADukeEnergyNarrows - Boiler #1

VADukeEnergyNarrows - Boiler #1

VADukeEnergyNarrows - Boiler #1

VADukeEnergyNarrows - Boiler #1

VADukeEnergyNarrows - Boiler #7

VADukeEnergyNarrows - Boiler #7

VADukeEnergyNarrows - Boiler #7

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

FLRayonierPerformance

MINeenahPaperMI Boiler 1- 7/25/2006

MINeenahPaperMI Boiler 1- 7/25/2006

MINeenahPaperMI Boiler 1- 7/25/2006

MINeenahPaperMI Boiler 1 - 8/1/2006

MINeenahPaperMI Boiler 1 - 8/1/2006

MINeenahPaperMI Boiler 1 - 8/1/2006

MNDESPHansONyman EU-07 - 3/6/2007

MNDESPHansONyman EU-07 - 3/6/2007

MNDESPHansONyman EU-07 - 3/6/2007

INPurdueUniverisity - Boiler 5 - 7/21/2009

INPurdueUniverisity - Boiler 5 - 7/21/2009

INPurdueUniverisity - Boiler 5 - 7/21/2009

NCGPRoxboro - ES-1 Wood fired Boiler - 7/14/2004

NCGPRoxboro - ES-1 Wood fired Boiler - 7/14/2004

NCGPRoxboro - ES-1 Wood fired Boiler - 7/14/2004

OHAppletonIdeas - Boiler 4 (B003) - 1/31/2003

OHAppletonIdeas - Boiler 4 (B003) - 1/31/2003

OHAppletonIdeas - Boiler 4 (B003) - 1/31/2003

OKGPMuskogeeMill B-3 - 5/20/2003

OKGPMuskogeeMill B-3 - 5/20/2003

OKGPMuskogeeMill B-3 - 5/20/2003

WIGPGreenBay2818 - B29 - Fluidized Bed Boiler #9 - 1992 - 

10/27/1992

WIGPGreenBay2818 - B29 - Fluidized Bed Boiler #9 - 1992 - 

10/27/1992

WIGPGreenBay2818 - B29 - Fluidized Bed Boiler #9 - 1992 - 

10/27/1992

Hg - Filter 

(1B)

Hg - Probe 

Wash (2B)

Hg - Nitric 

(3A)

Hg - 

Permanganate 

(3B)

Hg - HCl 

Rinse (3C) Notes ACTION

Pre-Corrected 

Hg Value 

(lb/mmBtu)

Reported Detection limits (ug)

0.1 0.2 1.52 0.5 0.4 Reported ND as zero. Do not change, NCASI submitted corrections 4.64E-07

0.1 0.2 1.52 0.5 0.4 Reported ND as zero. Do not change, NCASI submitted corrections 5.91E-07

0.015 0.57 No Data 0.025 0.25

Lab data lacks sample 3A, which is not an optional part of the sample. 

However, email from testing firm shows that omission of 3A did not affect 

measurement Do not change

0.015 0.49 No Data 0.025 0.25

Lab data lacks sample 3A, which is not an optional part of the sample. 

However, email from testing firm shows that omission of 3A did not affect 

measurement Do not change

0.015 0.51 No Data 0.025 0.25

Lab data lacks sample 3A, which is not an optional part of the sample. 

However, email from testing firm shows that omission of 3A did not affect 

measurement Do not change

0.4 0.9 0.2 0.2 1.2 Do not change

0.4 0.9 0.2 0.2 1.2 Do not change

0.4 0.9 0.2 0.2 1.2 Do not change

0.2 0.4 0.4 0.16 0.28 Reported ND as zero. Do not change, NCASI submitted corrections 4.10E-07

0.2 0.4 0.4 0.16 0.28 Reported ND as zero. Do not change, NCASI submitted corrections 5.60E-07

0.2 0.4 0.4 0.16 0.28 Reported ND as zero. Do not change, NCASI submitted corrections 4.30E-07

0.1 0.4 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 6.17E-07

0.1 0.4 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 2.78E-07

0.1 0.4 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 2.54E-07

0.1 0.2 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 5.07E-06

0.1 0.2 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 4.22E-06

0.1 0.2 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 4.02E-06

0.1 0.2 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 7.25E-07

0.1 0.2 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 5.99E-07

0.1 0.2 0.2 0.5 0.4 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z 6.90E-07

0.015 0.05 0.005 0.41 0.1 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.006 0.44 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.005 0.42 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.005 0.41 0.1 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.006 0.44 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.005 0.42 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.002 0.35 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.004 0.35 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

0.015 0.05 0.004 0.35 0.05 Reported ND as zero. Updated value to calculated lb/mmBtu value, Z

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data

Report did not provide lab data, however the calculations were able to be 

confirmed correct. Do not change

No Data No Data No Data No Data No Data

Report did not provide lab data, however the calculations were able to be 

confirmed correct. Do not change

No Data No Data No Data No Data No Data

Report did not provide lab data, however the calculations were able to be 

confirmed correct. Do not change

No Data No Data No Data No Data No Data

Report did not provide lab data. Tests for "engineering study" may not have 

been conducted to meet compliance or all method criteria. Remove test data from floor calculations

No Data No Data No Data No Data No Data

Report did not provide lab data. Tests for "engineering study" may not have 

been conducted to meet compliance or all method criteria. Remove test data from floor calculations

No Data No Data No Data No Data No Data

Report did not provide lab data. Tests for "engineering study" may not have 

been conducted to meet compliance or all method criteria. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Report did not provide lab data. Remove test data from floor calculations

No Data No Data No Data No Data No Data Impossible to confirm data as lab data is poorly labeled. Remove test data from floor calculations

No Data No Data No Data No Data No Data Impossible to confirm data as lab data is poorly labeled. Remove test data from floor calculations

No Data No Data No Data No Data No Data Impossible to confirm data as lab data is poorly labeled. Remove test data from floor calculations