Name: Jeffrey A. Smith

Title: PDG Regional Plant General Manager

Company: Florida Power & Light

Sign Date: 6/10/2010

Name: Thomas K. Graham

Title: Director of Operations

Company: Air Hygiene International, Inc.

Sign Date: 6/2/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Port Everglades Energy Center, Unit #4, Information Collection Request

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 14, 2011 Page 1 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Facility Information:

Port Everglades Energy Center

8100 Eisenhower Blvd 

Fort Lauderdale FL 33316

Contact: Augie De La Vega

Phone: (305)-242-3896

Fax:

Email: augie.de.la.vega@fpl.com

Testing Company:

Air Hygiene International, Inc.

5634 S. 122nd East Ave, Suite F

Tulsa OK 74146

Contact:Thomas Graham

Phone: (918) 307-8865

Fax: (918) 307-9131

Email: tom@airhygiene.com

Air Permit Number:

0110036-009-AV

Permitted Source ID/Name:

PPE4 Foster Wheeler, Wall Fired Boiler

Permitted Maximum Process Rate:

400 MW

Max. Normal Operation Process Rate:

380 MW

Target Process Test Rate

375 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster 

Wheeler design, designated as Units PPE3 and PPE4. The facility is located at 8100 Eisenhower Blvd in Fort 

Lauderdale, Florida. Unit PPE3 and PPE4 are of identical design and consists of two dry bottom, wall fired boilers 

and ancillary equipment designed to generate 400 megawatts (MW) of electricity each with rated heat inputs of 4,000 

million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). Fuel oil consumption is rated 

at 230,000 pounds per hour. Unit PPE3 and PPE4 utilize low nitrogen oxide (NOx) burner technology to control 

NOx emissions and electrostatic precipitators (ESPs) to control particulate matter (PM) emissions. Emission testing 

will be conducted from platforms on the independent stacks of each unit.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110036 FRS #: 110000363847

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

PPE4 - D/F 251 0 0 0 2592 1016 4 24

PPE4 - Gases 251 0 0 0 2592 1016 4 1

PPE4 - Metals 251 0 0 0 2592 1016 4 24

PPE4 - PM 251 0 0 0 2592 1016 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Regulation Description Compound Limit Unit

Not applicable.

Monday, February 14, 2011 Page 2 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

PPE4 - D/F % H2O Method 1 - 4 3 480 30

PPE4 - D/F 2,3,7,8-TCDD Method 23 3 480 30

PPE4 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 30

PPE4 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 30

PPE4 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 30

PPE4 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 30

PPE4 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 30

PPE4 - D/F OCDD Method 23 3 480 30

PPE4 - D/F 2,3,7,8-TCDF Method 23 3 480 30

PPE4 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 30

PPE4 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 30

PPE4 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 30

PPE4 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 30

PPE4 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 30

PPE4 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 30

PPE4 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 30

PPE4 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 30

PPE4 - D/F OCDF Method 23 3 480 30

PPE4 - D/F Total Dioxins Method 23 3 480 30

PPE4 - D/F Total Furans Method 23 3 480 30

PPE4 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 30

PPE4 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 30

PPE4 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 30

PPE4 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 30

PPE4 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 30

PPE4 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 30

PPE4 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 30

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

PPE4 - D/F Method 23 3 480 30

PPE4 - D/F 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 30

PPE4 - D/F 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 30

2,3,3',4,4',5,5'-HpCB 

(PCB189)

PPE4 - D/F Method 23 3 480 30

PPE4 - D/F O2 Method 3A O2 3 480 30

PPE4 - D/F Co2 Method 3A CO2 3 480 30

% H2O Method 1 - 4 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

Co2 Method 3A CO2 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

O2 Method 3A O2 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after 

initial stratification test

PPE4 - Gases

PPE4 - Metals % H2O Method 1 - 4 3 240 30

PPE4 - Metals Nickel Method 29 3 240 30

PPE4 - Metals Filterable Particulate Method 29 3 240 30

Monday, February 14, 2011 Page 3 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

PM Run 1 - vacuum maximized before end of run, did not pull required volume.
PM Run 2 and 3 - reduced to 2 

hour runs to avoid high vacuum, did not pull required volume.
PM All - oily substance on all filters

PPE4 - Metals Cobalt Method 29 3 240 30

PPE4 - Metals Chromium Method 29 3 240 30

PPE4 - Metals Cadmium Method 29 3 240 30

PPE4 - Metals Manganese Method 29 3 240 30

PPE4 - Metals Selenium Method 29 3 240 30

PPE4 - Metals Lead Method 29 3 240 30

PPE4 - Metals Co2 Method 3A CO2 3 240 30

PPE4 - Metals O2 Method 3A O2 3 240 30

% H2O Method 1 - 4 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Organic Condensible 

Particulate

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

O2 Method 3A O2 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based 

on method calculations

PPE4 - PM

Monday, February 14, 2011 Page 4 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Sampling / Stack Data Results Summary

Location PPE4 - D/F - Method 23

Average

Run Number PPE4-23-1 PPE4-23-2 PPE4-23-3

Test Date 3/16/2010 3/17/2010 3/18/2010

Run Start Time 12:30:00 PM 1:43:00 PM 12:28:00 PM

Run Finish Time 8:30:00 PM 9:43:00 PM 8:28:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 354.661 348.655 349.498 350.938

Moisture Content of Stack Gas, % 8.81 9.43 8.67 8.970

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14 13.9 14.04 13.980

Oxygen, % 4.08 4.41 4.01 4.167

Average Stack Gas Temperature, °F 314.83 320.83 318.13 317.930

Dry Volumetric Flow Rate, dry scfm 763,436.6 754,681.7 746,633.0 754,917.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,234,341.0 1,238,052.1 1,212,899.3 1,228,430.80

0

Percent Isokinetic of Sampling Rate, % 97.6 97.0 98.3 97.633

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PPE4 - Gases - Method 10

Average

Run Number 4-CO-1 4-CO-2 4-CO-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 5 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 25A

Average

Run Number 4-THC-1 4-THC-2 4-THC-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PPE4 - Gases - Method 3A CO2

Average

Run Number 4-CO2-1 4-CO2-2 4-CO2-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 6 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 3A O2

Average

Run Number 4-O2-1 4-O2-2 4-O2-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PPE4 - Gases - Method 6C

Average

Run Number 4-SO2-1 4-SO2-2 4-SO2-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 7 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 7E

Average

Run Number 4-NOx-1 4-NOx-2 4-NOx-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PPE4 - Metals - Method 29

Average

Run Number PPE4-29-1 PPE4-29-2 PPE4-29-3

Test Date 3/16/2010 3/17/2010 3/18/2010

Run Start Time 3:30:00 PM 2:30:00 PM 9:00:00 AM

Run Finish Time 7:30:00 PM 6:30:00 PM 1:00:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 174.489 181.398 612.219 322.702

Moisture Content of Stack Gas, % 9.47 9.97 3.01 7.483

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14 13.9 14.04 13.980

Oxygen, % 4.08 4.41 4.01 4.167

Average Stack Gas Temperature, °F 316.21 319.50 319.50 318.403

Dry Volumetric Flow Rate, dry scfm 734,828.4 761,437.7 786,948.2 761,071.433

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,198,879.7 1,257,019.7 1,207,126.5 1,221,008.63

3

Percent Isokinetic of Sampling Rate, % 99.7 100.1 326.8 175.533

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 8 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - PM - OTM - 27/28

Average

Run Number PPE4-27/28-

1

PPE4-

27/28-2

PPE4-27/28-

3

Test Date 3/16/2010 3/17/2010 3/18/2010

Run Start Time 9:04:00 AM 8:11:00 PM 2:48:00 PM

Run Finish Time 3:00:00 PM 10:08:00 

PM

4:56:00 PM

Net Run Time, minutes 288 118 120

Dry Gas Meter Volume Sampled, dscf 98.243 39.472 39.665 59.127

Moisture Content of Stack Gas, % 8.29 9.22 8.19 8.567

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14 13.9 14.04 13.980

Oxygen, % 4.08 4.41 4.01 4.167

Average Stack Gas Temperature, °F 314.33 320.25 318.17 317.583

Dry Volumetric Flow Rate, dry scfm 738,872.8 704,946.1 718,369.8 720,729.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,185,891.0 1,153,316.1 1,160,944.4 1,166,717.16

7

Percent Isokinetic of Sampling Rate, % 98.3 101.1 98.0 99.133

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 9 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Emissions Summary

Location: PPE4 - D/F - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.00000000666 0.0000000036 0.00000000992 0.000

lb/mmBtuO2 4.73E-13 2.65E-13 7.12E-13 0.000

ng/dscm 6.63E-04 3.65E-04 1.00E-03 0.001

ng/dscm@7%O2 5.48E-04 3.08E-04 8.23E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000016 0.0000000041 0.00000000678 0.000

lb/mmBtuO2 1.14E-13 3.02E-13 4.86E-13 0.000

ng/dscm 1.59E-04 4.15E-04 6.85E-04 0.000

ng/dscm@7%O2 1.31E-04 3.50E-04 5.64E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000021 0.0000000023 0.0000000023 0.000

lb/mmBtuO2 1.49E-13 1.69E-13 1.65E-13 0.000

ng/dscm 2.09E-04 2.33E-04 2.32E-04 0.000

ng/dscm@7%O2 1.73E-04 1.96E-04 1.91E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000011 0.0000000017 0.0000000025 0.000

lb/mmBtuO2 7.81E-14 1.25E-13 1.79E-13 0.000

ng/dscm 1.10E-04 1.72E-04 2.53E-04 0.000

ng/dscm@7%O2 9.09E-05 1.45E-04 2.08E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000011 0.0000000014 0.0000000017 0.000

lb/mmBtuO2 7.81E-14 1.03E-13 1.22E-13 0.000

ng/dscm 1.10E-04 1.42E-04 1.72E-04 0.000

ng/dscm@7%O2 9.09E-05 1.20E-04 1.42E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000011 0.0000000017 0.0000000025 0.000

lb/mmBtuO2 7.81E-14 1.25E-13 1.79E-13 0.000

ng/dscm 1.10E-04 1.72E-04 2.53E-04 0.000

ng/dscm@7%O2 9.09E-05 1.45E-04 2.08E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Monday, February 14, 2011 Page 10 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000011 0.0000000013 0.0000000015 0.000

lb/mmBtuO2 7.81E-14 9.57E-14 1.08E-13 0.000

ng/dscm 1.10E-04 1.32E-04 1.52E-04 0.000

ng/dscm@7%O2 9.09E-05 1.11E-04 1.25E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000011 0.0000000017 0.0000000025 0.000

lb/mmBtuO2 7.81E-14 1.25E-13 1.79E-13 0.000

ng/dscm 1.10E-04 1.72E-04 2.53E-04 0.000

ng/dscm@7%O2 9.09E-05 1.45E-04 2.08E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000012 0.0000000015 0.0000000018 0.000

lb/mmBtuO2 8.52E-14 1.10E-13 1.29E-13 0.000

ng/dscm 1.20E-04 1.52E-04 1.82E-04 0.000

ng/dscm@7%O2 9.92E-05 1.28E-04 1.50E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000014 0.0000000013 0.0000000021 0.000

lb/mmBtuO2 9.94E-14 9.57E-14 1.51E-13 0.000

ng/dscm 1.39E-04 1.32E-04 2.12E-04 0.000

ng/dscm@7%O2 1.15E-04 1.11E-04 1.74E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000019 0.0000000012 0.0000000014 0.000

lb/mmBtuO2 1.35E-13 8.84E-14 1.00E-13 0.000

ng/dscm 1.89E-04 1.22E-04 1.41E-04 0.000

ng/dscm@7%O2 1.56E-04 1.03E-04 1.16E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000019 0.0000000029 0.0000000122 0.000

lb/mmBtuO2 1.35E-13 2.14E-13 8.75E-13 0.000

ng/dscm 1.89E-04 2.94E-04 1.23E-03 0.001

ng/dscm@7%O2 1.56E-04 2.48E-04 1.01E-03 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.00000000842 0.0000000222 0.0000000493 0.000

lb/mmBtuO2 5.98E-13 1.64E-12 3.54E-12 0.000

ng/dscm 8.39E-04 2.25E-03 4.98E-03 0.003

ng/dscm@7%O2 6.93E-04 1.90E-03 4.10E-03 0.002

Monday, February 14, 2011 Page 11 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.000000201 0.000000373 0.000000833 0.000

lb/mmBtuO2 1.43E-11 2.75E-11 5.98E-11 0.000

ng/dscm 2.00E-02 3.78E-02 8.42E-02 0.047

ng/dscm@7%O2 1.65E-02 3.19E-02 6.93E-02 0.039

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.000000017 0.0000000474 0.000000102 0.000

lb/mmBtuO2 1.21E-12 3.49E-12 7.32E-12 0.000

ng/dscm 1.69E-03 4.80E-03 1.03E-02 0.006

ng/dscm@7%O2 1.40E-03 4.05E-03 8.48E-03 0.005

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000193 0.0000000285 0.0000000622 0.000

lb/mmBtuO2 1.37E-12 2.10E-12 4.46E-12 0.000

ng/dscm 1.92E-03 2.89E-03 6.29E-03 0.004

ng/dscm@7%O2 1.59E-03 2.44E-03 5.18E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.000000551 0.00000096 0.00000224 0.000

lb/mmBtuO2 3.91E-11 7.07E-11 1.61E-10 0.000

ng/dscm 5.49E-02 9.73E-02 2.26E-01 0.126

ng/dscm@7%O2 4.54E-02 8.20E-02 1.86E-01 0.104

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.00000001 0.000000014 0.0000000501 0.000

lb/mmBtuO2 7.10E-13 1.03E-12 3.59E-12 0.000

ng/dscm 9.96E-04 1.42E-03 5.06E-03 0.002

ng/dscm@7%O2 8.23E-04 1.20E-03 4.16E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000011 0.0000000013 0.0000000016 0.000

lb/mmBtuO2 7.81E-14 9.57E-14 1.15E-13 0.000

ng/dscm 1.10E-04 1.32E-04 1.62E-04 0.000

ng/dscm@7%O2 9.09E-05 1.11E-04 1.33E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.000000001 0.0000000011 0.0000000013 0.000

lb/mmBtuO2 7.10E-14 8.10E-14 9.33E-14 0.000

Monday, February 14, 2011 Page 12 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

ng/dscm 9.96E-05 1.11E-04 1.31E-04 0.000

ng/dscm@7%O2 8.23E-05 9.36E-05 1.08E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000019 0.000000003 0.0000000028 0.000

lb/mmBtuO2 1.35E-13 2.21E-13 2.01E-13 0.000

ng/dscm 1.89E-04 3.04E-04 2.83E-04 0.000

ng/dscm@7%O2 1.56E-04 2.56E-04 2.33E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.000000002 0.0000000031 0.0000000034 0.000

lb/mmBtuO2 1.42E-13 2.28E-13 2.44E-13 0.000

ng/dscm 1.99E-04 3.14E-04 3.44E-04 0.000

ng/dscm@7%O2 1.64E-04 2.65E-04 2.83E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.00000000065 0.00000000075 0.000000001 0.000

lb/mmBtuO2 4.61E-14 5.52E-14 7.17E-14 0.000

ng/dscm 6.47E-05 7.60E-05 1.01E-04 0.000

ng/dscm@7%O2 5.35E-05 6.41E-05 8.31E-05 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000021 0.0000000028 0.00000002 0.000

lb/mmBtuO2 1.49E-13 2.06E-13 1.43E-12 0.000

ng/dscm 2.09E-04 2.84E-04 2.02E-03 0.001

ng/dscm@7%O2 1.73E-04 2.39E-04 1.66E-03 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000891 0.000000154 0.000000374 0.000

lb/mmBtuO2 6.32E-12 1.13E-11 2.68E-11 0.000

ng/dscm 8.87E-03 1.56E-02 3.78E-02 0.021

ng/dscm@7%O2 7.33E-03 1.31E-02 3.11E-02 0.017

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000044 0.00000000649 0.0000000155 0.000

lb/mmBtuO2 3.12E-13 4.78E-13 1.11E-12 0.000

ng/dscm 4.38E-04 6.57E-04 1.57E-03 0.001

ng/dscm@7%O2 3.62E-04 5.54E-04 1.29E-03 0.001

Compound: OCDD

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Monday, February 14, 2011 Page 13 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Mass_mg 0.0000000082 0.00000001 0.000000027 0.000

lb/mmBtuO2 5.82E-13 7.37E-13 1.94E-12 0.000

ng/dscm 8.17E-04 1.01E-03 2.73E-03 0.002

ng/dscm@7%O2 6.75E-04 8.51E-04 2.25E-03 0.001

Compound: OCDF

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000084 0.0000000093 0.0000000052 0.000

lb/mmBtuO2 5.96E-13 6.85E-13 3.73E-13 0.000

ng/dscm 8.37E-04 9.42E-04 5.26E-04 0.001

ng/dscm@7%O2 6.92E-04 7.94E-04 4.33E-04 0.001

Compound: Total Dioxins

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.00000002146 0.000000023 0.00000004932 0.000

lb/mmBtuO2 1.52E-12 1.69E-12 3.54E-12 0.000

ng/dscm 2.14E-03 2.33E-03 4.98E-03 0.003

ng/dscm@7%O2 1.77E-03 1.96E-03 4.10E-03 0.003

Compound: Total Furans

Average

RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3

Mass_mg 0.0000000215 0.0000000266 0.00000002698 0.000

lb/mmBtuO2 1.53E-12 1.96E-12 1.94E-12 0.000

ng/dscm 2.14E-03 2.69E-03 2.73E-03 0.003

ng/dscm@7%O2 1.77E-03 2.27E-03 2.25E-03 0.002

Location: PPE4 - Gases - Method 10

Compound: Carbon Monoxide

Average

Run 4-CO-1 4-CO-2 4-CO-3

lb/mmBtuO2 4.61E-03 1.96E-03 2.04E-03 0.003

ppm 5.53E+00 2.37E+00 2.47E+00 3.457

ppm@7%O2 4.59E+00 1.95E+00 2.04E+00 2.860

Location: PPE4 - Gases - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 4-THC-1 4-THC-2 4-THC-3

lb/mmBtuO2 1.01E-03 1.06E-03 1.50E-05 0.001

ppm 7.71E-01 8.12E-01 1.15E-02 0.532

ppm@7%O2 6.41E-01 6.69E-01 9.48E-03 0.440

Location: PPE4 - Gases - Method 6C

Compound: Sulfur Dioxide

Average

Run 4-SO2-1 4-SO2-2 4-SO2-3

lb/mmBtuO2 1.04E+00 1.04E+00 1.03E+00 1.037

ppm 5.44E+02 5.50E+02 5.42E+02 545.333

ppm@7%O2 4.52E+02 4.53E+02 4.47E+02 450.667

Monday, February 14, 2011 Page 14 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location: PPE4 - Gases - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 4-NOx-1 4-NOx-2 4-NOx-3

lb/mmBtuO2 6.92E-01 6.89E-01 6.75E-01 0.685

ppm 5.05E+02 5.07E+02 4.97E+02 503.000

ppm@7%O2 4.20E+02 4.18E+02 4.10E+02 416.000

Location: PPE4 - Metals - Method 29

Compound: Antimony

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.000226 0.00148 0.00132 0.001

Elb/hr 1.26E-04 8.22E-04 2.24E-04 0.000

lb/mmBtuO2 3.26E-08 2.10E-07 5.41E-08 0.000

mg/dscm 4.57E-05 2.88E-04 7.62E-05 0.000

mg/dscm@7%O2 3.78E-05 2.43E-04 6.27E-05 0.000

Compound: Arsenic

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.002 0.002 0.00117 0.002

Elb/hr 1.11E-03 1.11E-03 1.99E-04 0.001

lb/mmBtuO2 2.89E-07 2.83E-07 4.79E-08 0.000

mg/dscm 4.05E-04 3.89E-04 6.75E-05 0.000

mg/dscm@7%O2 3.35E-04 3.28E-04 5.56E-05 0.000

Compound: Beryllium

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.0012 0.0012 0.0012 0.001

Elb/hr 6.68E-04 6.66E-04 2.04E-04 0.001

lb/mmBtuO2 1.73E-07 1.70E-07 4.91E-08 0.000

mg/dscm 2.43E-04 2.34E-04 6.92E-05 0.000

mg/dscm@7%O2 2.01E-04 1.97E-04 5.69E-05 0.000

Compound: Cadmium

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.0011 0.0011 0.0011 0.001

Elb/hr 6.13E-04 6.11E-04 1.87E-04 0.000

lb/mmBtuO2 1.59E-07 1.56E-07 4.50E-08 0.000

mg/dscm 2.23E-04 2.14E-04 6.35E-05 0.000

mg/dscm@7%O2 1.84E-04 1.80E-04 5.23E-05 0.000

Compound: Chromium

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.00206 0.00416 0.00993 0.005

Elb/hr 1.15E-03 2.31E-03 1.69E-03 0.002

lb/mmBtuO2 2.97E-07 5.89E-07 4.07E-07 0.000

mg/dscm 4.17E-04 8.10E-04 5.73E-04 0.001

Monday, February 14, 2011 Page 15 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

mg/dscm@7%O2 3.45E-04 6.83E-04 4.72E-04 0.001

Compound: Cobalt

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.029 0.00227 0.00252 0.011

Elb/hr 1.62E-02 1.26E-03 4.28E-04 0.006

lb/mmBtuO2 4.18E-06 3.21E-07 1.03E-07 0.000

mg/dscm 5.87E-03 4.42E-04 1.45E-04 0.002

mg/dscm@7%O2 4.85E-03 3.73E-04 1.19E-04 0.002

Compound: Filterable Particulate

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 4.2 2.5 2.5 3.067

Elb/hr 2.34E+00 1.39E+00 4.25E-01 1.385

lb/mmBtuO2 6.06E-04 3.54E-04 1.02E-04 0.000

mg/dscm 8.50E-01 4.87E-01 1.44E-01 0.494

mg/dscm@7%O2 7.02E-01 4.11E-01 1.19E-01 0.411

Compound: Lead

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.000653 0.0016 0.0022 0.001

Elb/hr 3.64E-04 8.88E-04 3.74E-04 0.001

lb/mmBtuO2 9.42E-08 2.26E-07 9.01E-08 0.000

mg/dscm 1.32E-04 3.12E-04 1.27E-04 0.000

mg/dscm@7%O2 1.09E-04 2.63E-04 1.05E-04 0.000

Compound: Manganese

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.00239 0.00677 0.00682 0.005

Elb/hr 1.33E-03 3.76E-03 1.16E-03 0.002

lb/mmBtuO2 3.45E-07 9.58E-07 2.79E-07 0.000

mg/dscm 4.84E-04 1.32E-03 3.93E-04 0.001

mg/dscm@7%O2 4.00E-04 1.11E-03 3.23E-04 0.001

Compound: Nickel

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.00663 0.0476 0.0511 0.035

Elb/hr 3.69E-03 2.64E-02 8.69E-03 0.013

lb/mmBtuO2 9.57E-07 6.74E-06 2.09E-06 0.000

mg/dscm 1.34E-03 9.27E-03 2.95E-03 0.005

mg/dscm@7%O2 1.11E-03 7.81E-03 2.43E-03 0.004

Compound: Selenium

Average

RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3

Mass_mg 0.02 0.0193 0.0211 0.020

Elb/hr 1.11E-02 1.07E-02 3.59E-03 0.008

lb/mmBtuO2 2.89E-06 2.73E-06 8.64E-07 0.000

mg/dscm 4.05E-03 3.76E-03 1.22E-03 0.003

Monday, February 14, 2011 Page 16 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Process Run Data

mg/dscm@7%O2 3.35E-03 3.17E-03 1.00E-03 0.003

Location: PPE4 - PM - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber PPE4-27/28-2 PPE4-27/28-3 PPE4-27/28-1

Mass_mg 17.675 11.8 14.125 14.533

lb/mmBtuO2 1.15E-02 7.46E-03 3.62E-03 0.008

Compound: Filterable PM2.5

Average

RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3

Mass_mg 12.6 17.15 7.275 12.342

lb/mmBtuO2 3.23E-03 1.12E-02 4.60E-03 0.006

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3

Mass_mg 2.727 12.199 30.602 15.176

lb/mmBtuO2 6.99E-04 7.94E-03 1.93E-02 0.009

Compound: Organic Condensible Particulate

Average

RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3

Mass_mg 4.05 3.55 21.85 9.817

lb/mmBtuO2 1.04E-03 2.31E-03 1.38E-02 0.006

Compound: Total Particulate

Average

RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3

Mass_mg 20.902 33.424 64.252 39.526

lb/mmBtuO2 5.36E-03 2.17E-02 4.06E-02 0.023

Compound: Total PM2.5

Average

RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3

Mass_mg 19.377 32.899 59.727 37.334

lb/mmBtuO2 4.97E-03 2.14E-02 3.78E-02 0.021

Monday, February 14, 2011 Page 17 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil (No. 6) Burned 28817 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/16/2010; 

Start - 09:28; 

End - 11:27

0

10 Residual Oil (No. 6) Burned 28521 gal/hr Method 027/028; 

Run PM-1; Date - 

3/16/2010; Start - 

09:04; End - 15:00

0

11 Residual Oil (No. 6) Burned 28287 gal/hr Method 027/028; 

Run PM-2; Date - 

3/17/2010; Start - 

20:11; End - 22:08

0

12 Residual Oil (No. 6) Burned 27994 gal/hr Method 027/028; 

Run PM-3; Date - 

3/18/2010; Start - 

14:48; End - 16:56

0

2 Residual Oil (No. 6) Burned 28173 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/16/2010; 

Start - 15:00; 

End - 16:59

0

3 Residual Oil (No. 6) Burned 28217 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/16/2010; 

Start - 17:40; 

End - 19:39

0

4 Residual Oil (No. 6) Burned 28214 gal/hr Method 23; Run 

D/F-1; Date - 

3/16/2010; Start - 

12:30; End - 21:19

0

5 Residual Oil (No. 6) Burned 28375 gal/hr Method 23; Run 

D/F-2; Date - 

3/17/2010; Start - 

13:43; End - 22:20

0

6 Residual Oil (No. 6) Burned 28067 gal/hr Method 23; Run 

D/F-3; Date - 

3/18/2010; Start - 

12:28; End - 20:48

0

7 Residual Oil (No. 6) Burned 28199 gal/hr Method 29; Run 

M-1; Date - 

3/16/2010; Start - 

15:30; End - 20:02

0

Monday, February 14, 2011 Page 18 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

8 Residual Oil (No. 6) Burned 28404 gal/hr Method 29; Run 

M-2; Date - 

3/17/2010; Start - 

14:30; End - 19:10

0

9 Residual Oil (No. 6) Burned 28141 gal/hr Method 29; Run 

M-3; Date - 

3/18/2010; Start - 

09:00; End - 13:37

0

1 Average Heat Input 3559 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/16/2010; 

Start - 09:28; 

End - 11:27

0

10 Average Heat Input 3523 MMBtu/hr Method 027/028; 

Run PM-1; Date - 

3/16/2010; Start - 

09:04; End - 15:00

0

11 Average Heat Input 3495 MMBtu/hr Method 027/028; 

Run PM-2; Date - 

3/17/2010; Start - 

20:11; End - 22:08

0

12 Average Heat Input 3458 MMBtu/hr Method 027/028; 

Run PM-3; Date - 

3/18/2010; Start - 

14:48; End - 16:56

0

2 Average Heat Input 3480 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/16/2010; 

Start - 15:00; 

End - 16:59

0

3 Average Heat Input 3485 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/16/2010; 

Start - 17:40; 

End - 19:39

0

4 Average Heat Input 3484 MMBtu/hr Method 23; Run 

D/F-1; Date - 

3/16/2010; Start - 

12:30; End - 21:19

0

5 Average Heat Input 3505 MMBtu/hr Method 23; Run 

D/F-2; Date - 

3/17/2010; Start - 

13:43; End - 22:20

0

6 Average Heat Input 3466 MMBtu/hr Method 23; Run 

D/F-3; Date - 

3/18/2010; Start - 

12:28; End - 20:48

0

Monday, February 14, 2011 Page 19 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

7 Average Heat Input 3483 MMBtu/hr Method 29; Run 

M-1; Date - 

3/16/2010; Start - 

15:30; End - 20:02

0

8 Average Heat Input 3509 MMBtu/hr Method 29; Run 

M-2; Date - 

3/17/2010; Start - 

14:30; End - 19:10

0

9 Average Heat Input 3476 MMBtu/hr Method 29; Run 

M-3; Date - 

3/18/2010; Start - 

09:00; End - 13:37

0

1 Steam Output 2372 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/16/2010; 

Start - 09:28; 

End - 11:27

0

10 Steam Output 2359 1000 lb Method 027/028; 

Run PM-1; Date - 

3/16/2010; Start - 

09:04; End - 15:00

0

11 Steam Output 2355 1000 lb Method 027/028; 

Run PM-2; Date - 

3/17/2010; Start - 

20:11; End - 22:08

0

12 Steam Output 2352 1000 lb Method 027/028; 

Run PM-3; Date - 

3/18/2010; Start - 

14:48; End - 16:56

0

2 Steam Output 2340 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/16/2010; 

Start - 15:00; 

End - 16:59

0

3 Steam Output 2345 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/16/2010; 

Start - 17:40; 

End - 19:39

0

4 Steam Output 2344 1000 lb Method 23; Run 

D/F-1; Date - 

3/16/2010; Start - 

12:30; End - 21:19

0

5 Steam Output 2371 1000 lb Method 23; Run 

D/F-2; Date - 

3/17/2010; Start - 

13:43; End - 22:20

0

Monday, February 14, 2011 Page 20 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

6 Steam Output 2352 1000 lb Method 23; Run 

D/F-3; Date - 

3/18/2010; Start - 

12:28; End - 20:48

0

7 Steam Output 2343 1000 lb Method 29; Run 

M-1; Date - 

3/16/2010; Start - 

15:30; End - 20:02

0

8 Steam Output 2379 1000 lb Method 29; Run 

M-2; Date - 

3/17/2010; Start - 

14:30; End - 19:10

0

9 Steam Output 2365 1000 lb Method 29; Run 

M-3; Date - 

3/18/2010; Start - 

09:00; End - 13:37

0

1 Unit Gross Electrical Output 377 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/16/2010; 

Start - 09:28; 

End - 11:27

0

10 Unit Gross Electrical Output 377 MWg Method 027/028; 

Run PM-1; Date - 

3/16/2010; Start - 

09:04; End - 15:00

0

11 Unit Gross Electrical Output 378 MWg Method 027/028; 

Run PM-2; Date - 

3/17/2010; Start - 

20:11; End - 22:08

0

12 Unit Gross Electrical Output 376 MWg Method 027/028; 

Run PM-3; Date - 

3/18/2010; Start - 

14:48; End - 16:56

0

2 Unit Gross Electrical Output 377 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/16/2010; 

Start - 15:00; 

End - 16:59

0

3 Unit Gross Electrical Output 377 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/16/2010; 

Start - 17:40; 

End - 19:39

0

4 Unit Gross Electrical Output 377 MWg Method 23; Run 

D/F-1; Date - 

3/16/2010; Start - 

12:30; End - 21:19

0

Monday, February 14, 2011 Page 21 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

5 Unit Gross Electrical Output 380 MWg Method 23; Run 

D/F-2; Date - 

3/17/2010; Start - 

13:43; End - 22:20

0

6 Unit Gross Electrical Output 377 MWg Method 23; Run 

D/F-3; Date - 

3/18/2010; Start - 

12:28; End - 20:48

0

7 Unit Gross Electrical Output 377 MWg Method 29; Run 

M-1; Date - 

3/16/2010; Start - 

15:30; End - 20:02

0

8 Unit Gross Electrical Output 381 MWg Method 29; Run 

M-2; Date - 

3/17/2010; Start - 

14:30; End - 19:10

0

9 Unit Gross Electrical Output 377 MWg Method 29; Run 

M-3; Date - 

3/18/2010; Start - 

09:00; End - 13:37

0

1 Unit Net Electric Generation 366 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/16/2010; 

Start - 09:28; 

End - 11:27

0

10 Unit Net Electric Generation 366 MWn Method 027/028; 

Run PM-1; Date - 

3/16/2010; Start - 

09:04; End - 15:00

0

11 Unit Net Electric Generation 366 MWn Method 027/028; 

Run PM-2; Date - 

3/17/2010; Start - 

20:11; End - 22:08

0

12 Unit Net Electric Generation 365 MWn Method 027/028; 

Run PM-3; Date - 

3/18/2010; Start - 

14:48; End - 16:56

0

2 Unit Net Electric Generation 365 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/16/2010; 

Start - 15:00; 

End - 16:59

0

3 Unit Net Electric Generation 365 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/16/2010; 

Start - 17:40; 

End - 19:39

0

Monday, February 14, 2011 Page 22 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

APCD Run Data

Process Lab Run Data

4 Unit Net Electric Generation 365 MWn Method 23; Run 

D/F-1; Date - 

3/16/2010; Start - 

12:30; End - 21:19

0

5 Unit Net Electric Generation 368 MWn Method 23; Run 

D/F-2; Date - 

3/17/2010; Start - 

13:43; End - 22:20

0

6 Unit Net Electric Generation 365 MWn Method 23; Run 

D/F-3; Date - 

3/18/2010; Start - 

12:28; End - 20:48

0

7 Unit Net Electric Generation 365 MWn Method 29; Run 

M-1; Date - 

3/16/2010; Start - 

15:30; End - 20:02

0

8 Unit Net Electric Generation 369 MWn Method 29; Run 

M-2; Date - 

3/17/2010; Start - 

14:30; End - 19:10

0

9 Unit Net Electric Generation 366 MWn Method 29; Run 

M-3; Date - 

3/18/2010; Start - 

09:00; End - 13:37

0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 477 NOx Emissions 0

2 LOW NOX BURNERS 452 NOx Emissions 0

3 LOW NOX BURNERS 449 NOx Emissions 0

1 ELECTROSTATIC PRECIPITATORS 3.4 Opacity 0

2 ELECTROSTATIC PRECIPITATORS 3.4 Opacity 0

3 ELECTROSTATIC PRECIPITATORS 3.3 Opacity 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 18100 Btu/lb

1 Fuel Moisture 0.807 %

1 Fuel Mercury Content 0.001 mg/kg

1 Fuel Chlorine Content 120 mg/kg

1 Fuel Fluorine Content 78 mg/kg

1 Fuel Antimony Content 1.1 mg/kg

1 Fuel Arsenic Content 0.049 mg/kg

1 Fuel Beryllium Content 0.008 mg/kg

Monday, February 14, 2011 Page 23 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

1 Fuel Cadmium Content 0.009 mg/kg

1 Fuel Chromium Content 0.098 mg/kg

1 Fuel Cobalt Content 1.1 mg/kg

1 Fuel Lead Content 0.21 mg/kg

1 Fuel Manganese Content 0.5 mg/kg

1 Fuel Nickel Content 23.6 mg/kg

1 Fuel Selenium Content 0.022 mg/kg

1 Fuel Sulfur Content 9760 mg/kg

1 Fuel Proximate Analysis (Carbon) 88.7 %

1 Fuel Proximate Analysis (Hydrogen) 10.16 %

1 Fuel Proximate Analysis (Nitrogen) 0.54 %

1 Fuel Proximate Analysis (Oxygen) 0.5 %

1 Fuel Proximate Analysis (Sulfur) 1.07 %

2 Fuel Higher Heating Value 18200 Btu/lb

2 Fuel Moisture 2.08 %

2 Fuel Mercury Content 0.001 mg/kg

2 Fuel Chlorine Content 140 mg/kg

2 Fuel Fluorine Content 65 mg/kg

2 Fuel Antimony Content 0.9 mg/kg

2 Fuel Arsenic Content 0.053 mg/kg

2 Fuel Beryllium Content 0.008 mg/kg

2 Fuel Cadmium Content 0.009 mg/kg

2 Fuel Chromium Content 0.092 mg/kg

2 Fuel Cobalt Content 1.1 mg/kg

2 Fuel Lead Content 0.2 mg/kg

2 Fuel Manganese Content 0.4 mg/kg

2 Fuel Nickel Content 23.4 mg/kg

2 Fuel Selenium Content 0.022 mg/kg

2 Fuel Sulfur Content 9500 mg/kg

2 Fuel Proximate Analysis (Carbon) 88.31 %

2 Fuel Proximate Analysis (Hydrogen) 9.96 %

2 Fuel Proximate Analysis (Nitrogen) 0.53 %

2 Fuel Proximate Analysis (Oxygen) 0.5 %

2 Fuel Proximate Analysis (Sulfur) 1.06 %

3 Fuel Higher Heating Value 18200 Btu/lb

3 Fuel Moisture 0.917 %

3 Fuel Mercury Content 0.001 mg/kg

3 Fuel Chlorine Content 120 mg/kg

3 Fuel Fluorine Content 78 mg/kg

3 Fuel Antimony Content 0.9 mg/kg

3 Fuel Arsenic Content 0.052 mg/kg

3 Fuel Beryllium Content 0.008 mg/kg

3 Fuel Cadmium Content 0.01 mg/kg

Monday, February 14, 2011 Page 24 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

3 Fuel Chromium Content 0.091 mg/kg

3 Fuel Cobalt Content 1.2 mg/kg

3 Fuel Lead Content 0.21 mg/kg

3 Fuel Manganese Content 0.4 mg/kg

3 Fuel Nickel Content 24.9 mg/kg

3 Fuel Selenium Content 0.022 mg/kg

3 Fuel Sulfur Content 9680 mg/kg

3 Fuel Proximate Analysis (Carbon) 87.94 %

3 Fuel Proximate Analysis (Hydrogen) 10.25 %

3 Fuel Proximate Analysis (Nitrogen) 0.55 %

3 Fuel Proximate Analysis (Oxygen) 0.5 %

3 Fuel Proximate Analysis (Sulfur) 1.07 %

Monday, February 14, 2011 Page 25 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Sampling / Stack Data Results Detail

Location PPE4 - D/F - Method 23

Average

Run Number PPE4-23-1 PPE4-23-2 PPE4-23-3

Test Date 3/16/2010 3/17/2010 3/18/2010

Run Start Time 12:30:00 PM 1:43:00 PM 12:28:00 PM

Run Finish Time 8:30:00 PM 9:43:00 PM 8:28:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.979 0.979 0.979 0.979

Barometric Pressure, inches of Mercury 29.71 29.71 29.65 29.690

Average Orifice Meter Differential, inches H2O 1.89 1.96 1.90 1.917

Dry Gas Meter Volume Sampled, cubic feet 370.510 358.170 365.490 364.723

Average Dry Gas Meter Temperature, °F 78.73 69.85 78.21 75.597

Dry Gas Meter Volume Sampled, dscf 354.661 348.655 349.498 350.938

Total Moisture Liquid collected, g 728 771 705.1 734.700

Volume of Water Vapor, standard cubic feet 34.27 36.29 33.19 34.583

Moisture Content of Stack Gas, % 8.81 9.43 8.67 8.970

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9119 0.9057 0.9133 0.910

Carbon Dioxide, % 14 13.9 14.04 13.980

Oxygen, % 4.08 4.41 4.01 4.167

Carbon Monoxide & Nitrogen, % 81.92 81.69 81.95 81.853

Fuel Factor 1.20 1.19 1.20

Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403

Wet Molecular weight, lb/lb-Mole 29.31 29.23 29.33 29.290

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.78 29.78 29.72 29.760

Average Stack Gas Temperature, °F 314.83 320.83 318.13 317.930

Average Velocity Head, inches of H2O 0.7828981180

58549

0.779615199

474394

0.751870450

466923

0.771

Average Stack Gas Velocity, feet/second 59.87 60.05 58.83 59.583

Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617

Dry Volumetric Flow Rate, dry scfm 763,436.6 754,681.7 746,633.0 754,917.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,234,341.0 1,238,052.1 1,212,899.3 1,228,430.8

00

Percent Isokinetic of Sampling Rate, % 97.6 97.0 98.3 97.633

Percent Excess Air, % 23.3 25.7 22.8 23.933

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 251 251 251

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 26 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 10

Average

Run Number 4-CO-1 4-CO-2 4-CO-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Analyzer Make THERMO THERMO THERMO

Analyzer Model 48i 48i 48i

Analyzer Serial Number INST-CO0017INST-CO0017INST-CO0017

Operating Range 9.2 9.2 9.2 9.200

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 5 5 5 5.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.23 0.25 0.27 0.250

Calibration Pre Zero Cylinder Bias 2.72 2.93 3.15 2.933

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AL1933 AL1933 AL1933

Calibration Pre High Cylinder Instrument Response 4.85 4.87 4.99 4.903

Calibration Pre High Cylinder Bias 0.22 0.43 1.74 0.797

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.25 0.27 0.28 0.267

Calibration Post Zero Cylinder Bias 2.93 3.15 3.26 3.113

Calibration Post Zero Cylinder Drift 0.21 0.22 0.11 0.180

Calibration Post High Cylinder ID AL1933 AL1933 AL1933

Calibration Post High Cylinder Instrument Response 4.87 4.99 5.27 5.043

Calibration Post High Cylinder Bias 0.43 1.74 4.78 2.317

Calibration Post High Cylinder Drift 0.21 1.31 3.04 1.520

Cavg 5.43 2.51 2.71 3.550

Cavg Units ppmvd ppmvd ppmvd

Cgas 5.527 2.3704 2.4676 3.455

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Monday, February 14, 2011 Page 27 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 25A

Average

Run Number 4-THC-1 4-THC-2 4-THC-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Analyzer Make VIG VIG VIG

Analyzer Model 20 20 20 20.000

Analyzer Serial Number INST-TH0007INST-TH0007INST-TH0007

Operating Range 50 50 50 50.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 6 6 6 6.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0 0.73 1.54 0.757

Calibration Pre Zero Cylinder Bias -0.14 1.32 2.94 1.373

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID CC115743 CC115743 CC115743

Calibration Pre High Cylinder Instrument Response 14.18 15.01 15.07 14.753

Calibration Pre High Cylinder Bias -0.58 1.08 1.2 0.567

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.73 1.54 1.3 1.190

Calibration Post Zero Cylinder Bias 1.32 2.94 2.46 2.240

Calibration Post Zero Cylinder Drift 1.46 1.62 0.48 1.187

Calibration Post High Cylinder ID CC115743 CC115743 CC115743

Calibration Post High Cylinder Instrument Response 15.01 15.07 15.13 15.070

Calibration Post High Cylinder Bias 1.08 1.2 1.32 1.200

Calibration Post High Cylinder Drift 1.66 0.12 0.12 0.633

Cavg 1.06 1.85 1.43 1.447

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.7713 0.8121 0.0115 0.532

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0.7033028812

36824

0.740453074

433657

1.052631578

94737E-02

0.485

Cgasw Units ppmvw ppmvw ppmvw

Monday, February 14, 2011 Page 28 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 3A CO2

Average

Run Number 4-CO2-1 4-CO2-2 4-CO2-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Analyzer Make THERMO THERMO THERMO

Analyzer Model 410i 410i 410i

Analyzer Serial Number INST-C2-0010 INST-C2-

0010

INST-C2-

0010

Operating Range 19.3 19.3 19.3 19.300

Operating Units % % %

No. Readings/Avg. 240 240 240 240.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.14 0.12 0.18 0.147

Calibration Pre Zero Cylinder Bias 0.62 0.52 0.83 0.657

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AAL12025-

CO2

AAL12025-

CO2

AAL12025-

CO2

Calibration Pre High Cylinder Instrument Response 8.94 8.88 9.01 8.943

Calibration Pre High Cylinder Bias 0.1 -0.21 0.47 0.120

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.12 0.18 0.43 0.243

Calibration Post Zero Cylinder Bias 0.52 0.83 2.12 1.157

Calibration Post Zero Cylinder Drift 0.1 0.31 1.29 0.567

Calibration Post High Cylinder ID AAL12025-

CO2

AAL12025-

CO2

AAL12025-

CO2

Calibration Post High Cylinder Instrument Response 8.88 9.01 9.4 9.097

Calibration Post High Cylinder Bias -0.21 0.47 2.49 0.917

Calibration Post High Cylinder Drift 0.31 0.68 2.02 1.003

Cavg 14 13.95 14.31 14.087

Cavg Units %vd %vd %vd

Cgas 14.0438 13.9491 13.9893 13.994

Cgas Units %vd %vd %vd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units %vw %vw %vw

Monday, February 14, 2011 Page 29 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 3A O2

Average

Run Number 4-O2-1 4-O2-2 4-O2-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Analyzer Make THERMO THERMO THERMO

Analyzer Model 42i-HL 42i-HL 42i-HL

Analyzer Serial Number INST-N2-0002 INST-N2-

0002

INST-N2-

0002

Operating Range 21.1 21.1 21.1 21.100

Operating Units % % %

No. Readings/Avg. 240 240 240 240.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.01 0.12 -0.08 0.017

Calibration Pre Zero Cylinder Bias 0.05 0.57 -0.38 0.080

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AAL12025-O2 AAL12025-

O2

AAL12025-

O2

Calibration Pre High Cylinder Instrument Response 12.02 11.99 11.87 11.960

Calibration Pre High Cylinder Bias -0.33 -0.47 -1.04 -0.613

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.12 -0.08 0 0.013

Calibration Post Zero Cylinder Bias 0.57 -0.38 0 0.063

Calibration Post Zero Cylinder Drift 0.52 0.95 0.38 0.617

Calibration Post High Cylinder ID AAL12025-O2 AAL12025-

O2

AAL12025-

O2

Calibration Post High Cylinder Instrument Response 11.99 11.87 11.95 11.937

Calibration Post High Cylinder Bias -0.47 -1.04 -0.66 -0.723

Calibration Post High Cylinder Drift 0.14 0.57 0.38 0.363

Cavg 4.18 3.99 3.94 4.037

Cavg Units %vd %vd %vd

Cgas 4.1701 4.0333 4.03 4.078

Cgas Units %vd %vd %vd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units %vw %vw %vw

Monday, February 14, 2011 Page 30 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 6C

Average

Run Number 4-SO2-1 4-SO2-2 4-SO2-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Analyzer Make THERMO THERMO THERMO

Analyzer Model 43i-HL 43i-HL 43i-HL

Analyzer Serial Number INST-S2-0005 INST-S2-

0005

INST-S2-

0005

Operating Range 959 959 959 959.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 6.7 5.07 8.8 6.857

Calibration Pre Zero Cylinder Bias 0.69 0.52 0.91 0.707

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID CC66246 CC66246 CC66246

Calibration Pre High Cylinder Instrument Response 412 417 422 417.000

Calibration Pre High Cylinder Bias -2.35 -1.82 -1.3 -1.823

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 5.07 8.8 9.02 7.630

Calibration Post Zero Cylinder Bias 0.52 0.91 0.93 0.787

Calibration Post Zero Cylinder Drift 0.17 0.39 0.02 0.193

Calibration Post High Cylinder ID CC66246 CC66246 CC66246

Calibration Post High Cylinder Instrument Response 417 422 422 420.333

Calibration Post High Cylinder Bias -1.82 -1.3 -1.3 -1.473

Calibration Post High Cylinder Drift 0.53 0.52 0 0.350

Cavg 524.96 537.14 532.18 531.427

Cavg Units ppmvd ppmvd ppmvd

Cgas 543.7003 550.0412 542.1568 545.299

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Monday, February 14, 2011 Page 31 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Gases - Method 7E

Average

Run Number 4-NOx-1 4-NOx-2 4-NOx-3

Test Date 3/16/2010 3/16/2010 3/16/2010

Run Start Time 9:28:19 AM 3:00:03 PM 5:40:03 PM

Run Finish Time 11:27:49 AM 4:59:33 PM 7:39:33 PM

Carbon Dioxide, % 14.04 13.95 13.99 13.993

Oxygen, % 4.17 4.03 4.03 4.077

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.82 8.82 8.82 8.820

Analyzer Make THERMO THERMO THERMO

Analyzer Model 42i-HL 42i-HL 42i-HL

Analyzer Serial Number INST-N2-0002 INST-N2-

0002

INST-N2-

0002

Operating Range 1110 1110 1110 1,110.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 1.23 7.73 10.87 6.610

Calibration Pre Zero Cylinder Bias 0.05 0.64 0.92 0.537

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID ALM042523 ALM042523 ALM042523

Calibration Pre High Cylinder Instrument Response 543 537 536.88 538.960

Calibration Pre High Cylinder Bias -1.09 -1.63 -1.64 -1.453

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 7.73 10.87 13.14 10.580

Calibration Post Zero Cylinder Bias 0.64 0.92 1.12 0.893

Calibration Post Zero Cylinder Drift 0.59 0.28 0.2 0.357

Calibration Post High Cylinder ID ALM042523 ALM042523 ALM042523

Calibration Post High Cylinder Instrument Response 537 536.88 543 538.960

Calibration Post High Cylinder Bias -1.63 -1.64 -1.09 -1.453

Calibration Post High Cylinder Drift 0.54 0.01 0.55 0.367

Cavg 498.4 498.15 491.64 496.063

Cavg Units ppmvd ppmvd ppmvd

Cgas 504.5082 506.7867 496.9558 502.750

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Monday, February 14, 2011 Page 32 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - Metals - Method 29

Average

Run Number PPE4-29-1 PPE4-29-2 PPE4-29-3

Test Date 3/16/2010 3/17/2010 3/18/2010

Run Start Time 3:30:00 PM 2:30:00 PM 9:00:00 AM

Run Finish Time 7:30:00 PM 6:30:00 PM 1:00:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.002 0.987 0.987 0.992

Barometric Pressure, inches of Mercury 29.71 29.65 29.62 29.660

Average Orifice Meter Differential, inches H2O 1.83 2.03 1.93 1.930

Dry Gas Meter Volume Sampled, cubic feet 178.370 187.590 624.640 330.200

Average Dry Gas Meter Temperature, °F 79.46 76.75 68.90 75.037

Dry Gas Meter Volume Sampled, dscf 174.489 181.398 612.219 322.702

Total Moisture Liquid collected, g 387.8 426.6 403.7 406.033

Volume of Water Vapor, standard cubic feet 18.25 20.08 19.00 19.110

Moisture Content of Stack Gas, % 9.47 9.97 3.01 7.483

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9053 0.9003 0.9699 0.925

Carbon Dioxide, % 14 13.9 14.04 13.980

Oxygen, % 4.08 4.41 4.01 4.167

Carbon Monoxide & Nitrogen, % 81.92 81.69 81.95 81.853

Fuel Factor 1.20 1.19 1.20

Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403

Wet Molecular weight, lb/lb-Mole 29.23 29.16 30.04 29.477

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.78 29.72 29.69 29.730

Average Stack Gas Temperature, °F 316.21 319.50 319.50 318.403

Average Velocity Head, inches of H2O 0.7353081038

27522

0.801331824

364615

0.760726953

506861

0.766

Average Stack Gas Velocity, feet/second 58.15 60.97 58.55 59.223

Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617

Dry Volumetric Flow Rate, dry scfm 734,828.4 761,437.7 786,948.2 761,071.433

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,198,879.7 1,257,019.7 1,207,126.5 1,221,008.6

33

Percent Isokinetic of Sampling Rate, % 99.7 100.1 326.8 175.533

Percent Excess Air, % 23.3 25.7 22.8 23.933

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 251 251 251

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 33 of 34
Port Everglades Energy Center, Unit #4, Information Collection Request

6/10/2010

Location PPE4 - PM - OTM - 27/28

Average

Run Number PPE4-27/28-1 PPE4-27/28-

2

PPE4-27/28-3

Test Date 3/16/2010 3/17/2010 3/18/2010

Run Start Time 9:04:00 AM 8:11:00 PM 2:48:00 PM

Run Finish Time 3:00:00 PM 10:08:00 PM 4:56:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 288 118 120

Nozzle Diameter, inches 0.172 0.172 0.172 0.172

Pitot Tube Coefficient 0.8 0.8 0.8 0.800

Dry Gas Meter Calibration Factor 1.002 0.987 0.987 0.992

Barometric Pressure, inches of Mercury 29.74 29.7 29.65 29.697

Average Orifice Meter Differential, inches H2O 0.39 0.40 0.40 0.397

Dry Gas Meter Volume Sampled, cubic feet 99.510 40.880 40.900 60.430

Average Dry Gas Meter Temperature, °F 73.17 76.29 73.04 74.167

Dry Gas Meter Volume Sampled, dscf 98.243 39.472 39.665 59.127

Total Moisture Liquid collected, g 188.7 85.2 75.2 116.367

Volume of Water Vapor, standard cubic feet 8.88 4.01 3.54 5.477

Moisture Content of Stack Gas, % 8.29 9.22 8.19 8.567

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9171 0.9078 0.9181 0.914

Carbon Dioxide, % 14 13.9 14.04 13.980

Oxygen, % 4.08 4.41 4.01 4.167

Carbon Monoxide & Nitrogen, % 81.92 81.69 81.95 81.853

Fuel Factor 1.20 1.19 1.20

Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403

Wet Molecular weight, lb/lb-Mole 29.37 29.26 29.39 29.340

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.81 29.77 29.72 29.767

Average Stack Gas Temperature, °F 314.33 320.25 318.17 317.583

Average Velocity Head, inches of H2O 0.7998552239

02578

0.746789430

998787

0.761009953

722415

0.769

Average Stack Gas Velocity, feet/second 57.52 55.94 56.31 56.590

Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617

Dry Volumetric Flow Rate, dry scfm 738,872.8 704,946.1 718,369.8 720,729.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,185,891.0 1,153,316.1 1,160,944.4 1,166,717.1

67

Percent Isokinetic of Sampling Rate, % 98.3 101.1 98.0 99.133

Percent Excess Air, % 23.3 25.7 22.8 23.933

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 251 251 251

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 34 of 34