### Name: Jeffrey A. Smith

Title: PDG Regional Plant General Manager Company: Florida Power & Light Sign Date: 6/10/2010 Name: Thomas K. Graham Title: Director of Operations Company:Air Hygiene International, Inc. Sign Date: 6/2/2010 Permitted Facility Representative / Date Testing Company Representative / Date



## Port Everglades Energy Center, Unit #4, Information Collection Request Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, February 14, 2011 Page 1 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Facility Information: Port Everglades Energy Center
8100 Eisenhower Blvd

Fort Lauderdale FL33316 Contact:Augie De La Vega Phone:(305)-242-3896 Fax: Email: augie.de.la.vega@fpl.com Testing Company: Air Hygiene International, Inc. 5634 S. 122nd East Ave, Suite F

Tulsa OK74146 Contact:Thomas Graham Phone:(918) 307-8865 Fax: (918) 307-9131 Email:tom@airhygiene.com

Air Permit Number: 0110036-009-AV Permitted Source ID/Name: Foster Wheeler, Wall Fired Boiler PPE4 Permitted Maximum Process Rate: 400 MW Max. Normal Operation Process Rate: 380 MW Target Process Test Rate 375 MW

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster Wheeler design, designated as Units PPE3 and PPE4. The facility is located at 8100 Eisenhower Blvd in Fort Lauderdale, Florida. Unit PPE3 and PPE4 are of identical design and consists of two dry bottom, wall fired boilers and ancillary equipment designed to generate 400 megawatts (MW) of electricity each with rated heat inputs of 4,000 million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). Fuel oil consumption is rated at 230,000 pounds per hour. Unit PPE3 and PPE4 utilize low nitrogen oxide (NOx) burner technology to control NOx emissions and electrostatic precipitators (ESPs) to control particulate matter (PM) emissions. Emission testing will be conducted from platforms on the independent stacks of each unit. Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:110036 FRS #:110000363847

SCC / Description10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width PPE4 - D/F 251 2592 1016 4 0 24 0 0 PPE4 - Gases 251 2592 1016 4 0 1 0 0 PPE4 - Metals 251 2592 1016 4 0 24 0 0 PPE4 - PM 251 2592 1016 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Regulation Description Compound Limit Unit Not applicable.



### Monday, February 14, 2011 Page 2 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location % H2O Method 1 - 4 3 480 30 PPE4 - D/F 2,3,7,8-TCDD Method 23 3 480 30 PPE4 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 30 PPE4 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 30 PPE4 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 30 PPE4 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 30 PPE4 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 30 PPE4 - D/F OCDD Method 23 3 480 30 PPE4 - D/F 2,3,7,8-TCDF Method 23 3 480 30 PPE4 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 30 PPE4 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 30 PPE4 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 30 PPE4 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 30 PPE4 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 30 PPE4 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 30 PPE4 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 30 PPE4 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 30 PPE4 - D/F OCDF Method 23 3 480 30 PPE4 - D/F Total Dioxins Method 23 3 480 30 PPE4 - D/F Total Furans Method 23 3 480 30 PPE4 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 30 PPE4 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 30 PPE4 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 30 PPE4 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 30 PPE4 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 30 PPE4 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 30 PPE4 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 30 PPE4 - D/F 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 30 PPE4 - D/F
2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 30 PPE4 - D/F 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 30 PPE4 - D/F 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 30 PPE4 - D/F

O2 Method 3A O2 3 480 30 PPE4 - D/F Co2 Method 3A CO2 3 480 30 PPE4 - D/F % H2O Method 1 - 4 3 120 1 Determined after initial stratification test PPE4 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after initial stratification test PPE4 - Gases
Total organic compounds

(TOC) as Propane Method 25A 3 120 1 Determined after initial stratification test PPE4 - Gases

Co2 Method 3A CO2 3 120 1 Determined after initial stratification test PPE4 - Gases

O2 Method 3A O2 3 120 1 Determined after initial stratification test PPE4 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after initial stratification test PPE4 - Gases
Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after initial stratification test PPE4 - Gases

% H2O Method 1 - 4 3 240 30 PPE4 - MetalsNickel Method 29 3 240 30 PPE4 - MetalsFilterable Particulate Method 29 3 240 30 PPE4 - Metals


### Monday, February 14, 2011 Page 3 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. PM Run 1 - vacuum maximized before end of run, did not pull required volume.
PM Run 2 and 3 - reduced to 2 hour runs to avoid high vacuum, did not pull required volume.
PM All - oily substance on all filters

Cobalt Method 29 3 240 30 PPE4 - MetalsChromium Method 29 3 240 30 PPE4 - MetalsCadmium Method 29 3 240 30 PPE4 - MetalsManganese Method 29 3 240 30 PPE4 - MetalsSelenium Method 29 3 240 30 PPE4 - MetalsLead Method 29 3 240 30 PPE4 - MetalsCo2 Method 3A CO2 3 240 30 PPE4 - MetalsO2 Method 3A O2 3 240 30 PPE4 - Metals% H2O Method 1 - 4 3 120 12 Run times vary based on method calculations PPE4 - PM
Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 120 12 Run times vary based on method calculations PPE4 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based on method calculations PPE4 - PM
Organic Condensible

Particulate OTM - 27/28 3 120 12 Run times vary based on method calculations PPE4 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based on method calculations PPE4 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based on method calculations PPE4 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based on method calculations PPE4 - PM

O2 Method 3A O2 3 120 12 Run times vary based on method calculations PPE4 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based on method calculations PPE4 - PM



### Monday, February 14, 2011 Page 4 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Sampling / Stack Data Results Summary


### Location PPE4 - D/F - Method 23 Average Run Number PPE4-23-1 PPE4-23-2 PPE4-23-3
Test Date 3/16/2010 3/17/2010 3/18/2010 Run Start Time 12:30:00 PM1:43:00 PM12:28:00 PM Run Finish Time 8:30:00 PM9:43:00 PM 8:28:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 354.661 348.655 349.498 350.938 Moisture Content of Stack Gas, % 8.81 9.43 8.67 8.970 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14 13.9 14.04 13.980 Oxygen, % 4.08 4.41 4.01 4.167 Average Stack Gas Temperature, °F 314.83 320.83 318.13 317.930 Dry Volumetric Flow Rate, dry scfm 763,436.6 754,681.7 746,633.0 754,917.100 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,234,341.01,238,052.1 1,212,899.31,228,430.80 0 Percent Isokinetic of Sampling Rate, % 97.6 97.0 98.3 97.633 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Location PPE4 - Gases - Method 10 Average Run Number 4-CO-1 4-CO-2 4-CO-3
Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 5 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 25A Average Run Number 4-THC-1 4-THC-2 4-THC-3
Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Location PPE4 - Gases - Method 3A CO2 Average Run Number 4-CO2-1 4-CO2-2 4-CO2-3
Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 6 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 3A O2 Average Run Number 4-O2-1 4-O2-2 4-O2-3
Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Location PPE4 - Gases - Method 6C Average Run Number 4-SO2-1 4-SO2-2 4-SO2-3
Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 7 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 7E Average Run Number 4-NOx-1 4-NOx-2 4-NOx-3
Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731 765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Location PPE4 - Metals - Method 29 Average Run Number PPE4-29-1 PPE4-29-2 PPE4-29-3
Test Date 3/16/2010 3/17/2010 3/18/2010 Run Start Time 3:30:00 PM2:30:00 PM 9:00:00 AM Run Finish Time 7:30:00 PM6:30:00 PM 1:00:00 PM Net Run Time, minutes 240 240 240 Dry Gas Meter Volume Sampled, dscf 174.489 181.398 612.219 322.702 Moisture Content of Stack Gas, % 9.47 9.97 3.01 7.483 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14 13.9 14.04 13.980 Oxygen, % 4.08 4.41 4.01 4.167 Average Stack Gas Temperature, °F 316.21 319.50 319.50 318.403 Dry Volumetric Flow Rate, dry scfm 734,828.4 761,437.7 786,948.2 761,071.433 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,198,879.71,257,019.7 1,207,126.51,221,008.63 3 Percent Isokinetic of Sampling Rate, % 99.7 100.1 326.8 175.533 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 8 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - PM - OTM - 27/28 Average Run Number PPE4-27/28- 1 PPE4- 27/28-2PPE4-27/28-

3
Test Date 3/16/2010 3/17/2010 3/18/2010 Run Start Time 9:04:00 AM8:11:00 PM 2:48:00 PM Run Finish Time 3:00:00 PM 10:08:00 PM 4:56:00 PM

Net Run Time, minutes 288 118 120 Dry Gas Meter Volume Sampled, dscf 98.243 39.472 39.665 59.127 Moisture Content of Stack Gas, % 8.29 9.22 8.19 8.567 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14 13.9 14.04 13.980 Oxygen, % 4.08 4.41 4.01 4.167 Average Stack Gas Temperature, °F 314.33 320.25 318.17 317.583 Dry Volumetric Flow Rate, dry scfm 738,872.8 704,946.1 718,369.8 720,729.567 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,185,891.01,153,316.1 1,160,944.41,166,717.16 7 Percent Isokinetic of Sampling Rate, % 98.3 101.1 98.0 99.133 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 9 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Emissions Summary


### Location: PPE4 - D/F - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.00000000666 0.0000000036 0.00000000992 0.000 lb/mmBtuO2 4.73E-13 2.65E-13 7.12E-13 0.000 ng/dscm 6.63E-04 3.65E-04 1.00E-03 0.001 ng/dscm@7%O2 5.48E-04 3.08E-04 8.23E-04 0.001 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000016 0.0000000041 0.00000000678 0.000 lb/mmBtuO2 1.14E-13 3.02E-13 4.86E-13 0.000 ng/dscm 1.59E-04 4.15E-04 6.85E-04 0.000 ng/dscm@7%O2 1.31E-04 3.50E-04 5.64E-04 0.000 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000021 0.0000000023 0.0000000023 0.000 lb/mmBtuO2 1.49E-13 1.69E-13 1.65E-13 0.000 ng/dscm 2.09E-04 2.33E-04 2.32E-04 0.000 ng/dscm@7%O2 1.73E-04 1.96E-04 1.91E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000011 0.0000000017 0.0000000025 0.000 lb/mmBtuO2 7.81E-14 1.25E-13 1.79E-13 0.000 ng/dscm 1.10E-04 1.72E-04 2.53E-04 0.000 ng/dscm@7%O2 9.09E-05 1.45E-04 2.08E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000011 0.0000000014 0.0000000017 0.000 lb/mmBtuO2 7.81E-14 1.03E-13 1.22E-13 0.000 ng/dscm 1.10E-04 1.42E-04 1.72E-04 0.000 ng/dscm@7%O2 9.09E-05 1.20E-04 1.42E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000011 0.0000000017 0.0000000025 0.000 lb/mmBtuO2 7.81E-14 1.25E-13 1.79E-13 0.000 ng/dscm 1.10E-04 1.72E-04 2.53E-04 0.000 ng/dscm@7%O2 9.09E-05 1.45E-04 2.08E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDF Average



### Monday, February 14, 2011 Page 10 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000011 0.0000000013 0.0000000015 0.000 lb/mmBtuO2 7.81E-14 9.57E-14 1.08E-13 0.000 ng/dscm 1.10E-04 1.32E-04 1.52E-04 0.000 ng/dscm@7%O2 9.09E-05 1.11E-04 1.25E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000011 0.0000000017 0.0000000025 0.000 lb/mmBtuO2 7.81E-14 1.25E-13 1.79E-13 0.000 ng/dscm 1.10E-04 1.72E-04 2.53E-04 0.000 ng/dscm@7%O2 9.09E-05 1.45E-04 2.08E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000012 0.0000000015 0.0000000018 0.000 lb/mmBtuO2 8.52E-14 1.10E-13 1.29E-13 0.000 ng/dscm 1.20E-04 1.52E-04 1.82E-04 0.000 ng/dscm@7%O2 9.92E-05 1.28E-04 1.50E-04 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000014 0.0000000013 0.0000000021 0.000 lb/mmBtuO2 9.94E-14 9.57E-14 1.51E-13 0.000 ng/dscm 1.39E-04 1.32E-04 2.12E-04 0.000 ng/dscm@7%O2 1.15E-04 1.11E-04 1.74E-04 0.000 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000019 0.0000000012 0.0000000014 0.000 lb/mmBtuO2 1.35E-13 8.84E-14 1.00E-13 0.000 ng/dscm 1.89E-04 1.22E-04 1.41E-04 0.000 ng/dscm@7%O2 1.56E-04 1.03E-04 1.16E-04 0.000 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000019 0.0000000029 0.0000000122 0.000 lb/mmBtuO2 1.35E-13 2.14E-13 8.75E-13 0.000 ng/dscm 1.89E-04 2.94E-04 1.23E-03 0.001 ng/dscm@7%O2 1.56E-04 2.48E-04 1.01E-03 0.000 

### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.00000000842 0.0000000222 0.0000000493 0.000 lb/mmBtuO2 5.98E-13 1.64E-12 3.54E-12 0.000 ng/dscm 8.39E-04 2.25E-03 4.98E-03 0.003 ng/dscm@7%O2 6.93E-04 1.90E-03 4.10E-03 0.002



### Monday, February 14, 2011 Page 11 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.000000201 0.000000373 0.000000833 0.000 lb/mmBtuO2 1.43E-11 2.75E-11 5.98E-11 0.000 ng/dscm 2.00E-02 3.78E-02 8.42E-02 0.047 ng/dscm@7%O2 1.65E-02 3.19E-02 6.93E-02 0.039 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.000000017 0.0000000474 0.000000102 0.000 lb/mmBtuO2 1.21E-12 3.49E-12 7.32E-12 0.000 ng/dscm 1.69E-03 4.80E-03 1.03E-02 0.006 ng/dscm@7%O2 1.40E-03 4.05E-03 8.48E-03 0.005 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000193 0.0000000285 0.0000000622 0.000 lb/mmBtuO2 1.37E-12 2.10E-12 4.46E-12 0.000 ng/dscm 1.92E-03 2.89E-03 6.29E-03 0.004 ng/dscm@7%O2 1.59E-03 2.44E-03 5.18E-03 0.003 

### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.000000551 0.00000096 0.00000224 0.000 lb/mmBtuO2 3.91E-11 7.07E-11 1.61E-10 0.000 ng/dscm 5.49E-02 9.73E-02 2.26E-01 0.126 ng/dscm@7%O2 4.54E-02 8.20E-02 1.86E-01 0.104 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.00000001 0.000000014 0.0000000501 0.000 lb/mmBtuO2 7.10E-13 1.03E-12 3.59E-12 0.000 ng/dscm 9.96E-04 1.42E-03 5.06E-03 0.002 ng/dscm@7%O2 8.23E-04 1.20E-03 4.16E-03 0.002 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000011 0.0000000013 0.0000000016 0.000 lb/mmBtuO2 7.81E-14 9.57E-14 1.15E-13 0.000 ng/dscm 1.10E-04 1.32E-04 1.62E-04 0.000 ng/dscm@7%O2 9.09E-05 1.11E-04 1.33E-04 0.000 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.000000001 0.0000000011 0.0000000013 0.000 lb/mmBtuO2 7.10E-14 8.10E-14 9.33E-14 0.000



### Monday, February 14, 2011 Page 12 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 ng/dscm 9.96E-05 1.11E-04 1.31E-04 0.000 ng/dscm@7%O2 8.23E-05 9.36E-05 1.08E-04 0.000 

### Compound: 2,3,7,8-TCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000019 0.000000003 0.0000000028 0.000 lb/mmBtuO2 1.35E-13 2.21E-13 2.01E-13 0.000 ng/dscm 1.89E-04 3.04E-04 2.83E-04 0.000 ng/dscm@7%O2 1.56E-04 2.56E-04 2.33E-04 0.000 

### Compound: 2,3,7,8-TCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.000000002 0.0000000031 0.0000000034 0.000 lb/mmBtuO2 1.42E-13 2.28E-13 2.44E-13 0.000 ng/dscm 1.99E-04 3.14E-04 3.44E-04 0.000 ng/dscm@7%O2 1.64E-04 2.65E-04 2.83E-04 0.000 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.00000000065 0.00000000075 0.000000001 0.000 lb/mmBtuO2 4.61E-14 5.52E-14 7.17E-14 0.000 ng/dscm 6.47E-05 7.60E-05 1.01E-04 0.000 ng/dscm@7%O2 5.35E-05 6.41E-05 8.31E-05 0.000 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000021 0.0000000028 0.00000002 0.000 lb/mmBtuO2 1.49E-13 2.06E-13 1.43E-12 0.000 ng/dscm 2.09E-04 2.84E-04 2.02E-03 0.001 ng/dscm@7%O2 1.73E-04 2.39E-04 1.66E-03 0.001 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000891 0.000000154 0.000000374 0.000 lb/mmBtuO2 6.32E-12 1.13E-11 2.68E-11 0.000 ng/dscm 8.87E-03 1.56E-02 3.78E-02 0.021 ng/dscm@7%O2 7.33E-03 1.31E-02 3.11E-02 0.017 

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000044 0.00000000649 0.0000000155 0.000 lb/mmBtuO2 3.12E-13 4.78E-13 1.11E-12 0.000 ng/dscm 4.38E-04 6.57E-04 1.57E-03 0.001 ng/dscm@7%O2 3.62E-04 5.54E-04 1.29E-03 0.001 

### Compound: OCDD Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3


### Monday, February 14, 2011 Page 13 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Mass_mg 0.0000000082 0.00000001 0.000000027 0.000 lb/mmBtuO2 5.82E-13 7.37E-13 1.94E-12 0.000 ng/dscm 8.17E-04 1.01E-03 2.73E-03 0.002 ng/dscm@7%O2 6.75E-04 8.51E-04 2.25E-03 0.001 

### Compound: OCDF Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000084 0.0000000093 0.0000000052 0.000 lb/mmBtuO2 5.96E-13 6.85E-13 3.73E-13 0.000 ng/dscm 8.37E-04 9.42E-04 5.26E-04 0.001 ng/dscm@7%O2 6.92E-04 7.94E-04 4.33E-04 0.001 

### Compound: Total Dioxins Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.00000002146 0.000000023 0.00000004932 0.000 lb/mmBtuO2 1.52E-12 1.69E-12 3.54E-12 0.000 ng/dscm 2.14E-03 2.33E-03 4.98E-03 0.003 ng/dscm@7%O2 1.77E-03 1.96E-03 4.10E-03 0.003 

### Compound: Total Furans Average RunNumber PPE4-23-1 PPE4-23-2 PPE4-23-3 Mass_mg 0.0000000215 0.0000000266 0.00000002698 0.000 lb/mmBtuO2 1.53E-12 1.96E-12 1.94E-12 0.000 ng/dscm 2.14E-03 2.69E-03 2.73E-03 0.003 ng/dscm@7%O2 1.77E-03 2.27E-03 2.25E-03 0.002



### Location: PPE4 - Gases - Method 10 Compound: Carbon Monoxide Average Run 4-CO-1 4-CO-2 4-CO-3 lb/mmBtuO2 4.61E-03 1.96E-03 2.04E-03 0.003 ppm 5.53E+00 2.37E+00 2.47E+00 3.457 ppm@7%O2 4.59E+00 1.95E+00 2.04E+00 2.860



### Location: PPE4 - Gases - Method 25A Compound: Total organic compounds (TOC) as Average Run 4-THC-1 4-THC-2 4-THC-3 lb/mmBtuO2 1.01E-03 1.06E-03 1.50E-05 0.001 ppm 7.71E-01 8.12E-01 1.15E-02 0.532 ppm@7%O2 6.41E-01 6.69E-01 9.48E-03 0.440



### Location: PPE4 - Gases - Method 6C Compound: Sulfur Dioxide Average Run 4-SO2-1 4-SO2-2 4-SO2-3 lb/mmBtuO2 1.04E+00 1.04E+00 1.03E+00 1.037 ppm 5.44E+02 5.50E+02 5.42E+02 545.333 ppm@7%O2 4.52E+02 4.53E+02 4.47E+02 450.667



### Monday, February 14, 2011 Page 14 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010

Location: PPE4 - Gases - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 4-NOx-1 4-NOx-2 4-NOx-3 lb/mmBtuO2 6.92E-01 6.89E-01 6.75E-01 0.685 ppm 5.05E+02 5.07E+02 4.97E+02 503.000 ppm@7%O2 4.20E+02 4.18E+02 4.10E+02 416.000



### Location: PPE4 - Metals - Method 29 

### Compound: Antimony Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.000226 0.00148 0.00132 0.001 Elb/hr 1.26E-04 8.22E-04 2.24E-04 0.000 lb/mmBtuO2 3.26E-08 2.10E-07 5.41E-08 0.000 mg/dscm 4.57E-05 2.88E-04 7.62E-05 0.000 mg/dscm@7%O2 3.78E-05 2.43E-04 6.27E-05 0.000 

### Compound: Arsenic Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.002 0.002 0.00117 0.002 Elb/hr 1.11E-03 1.11E-03 1.99E-04 0.001 lb/mmBtuO2 2.89E-07 2.83E-07 4.79E-08 0.000 mg/dscm 4.05E-04 3.89E-04 6.75E-05 0.000 mg/dscm@7%O2 3.35E-04 3.28E-04 5.56E-05 0.000 

### Compound: Beryllium Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.0012 0.0012 0.0012 0.001 Elb/hr 6.68E-04 6.66E-04 2.04E-04 0.001 lb/mmBtuO2 1.73E-07 1.70E-07 4.91E-08 0.000 mg/dscm 2.43E-04 2.34E-04 6.92E-05 0.000 mg/dscm@7%O2 2.01E-04 1.97E-04 5.69E-05 0.000 

### Compound: Cadmium Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.0011 0.0011 0.0011 0.001 Elb/hr 6.13E-04 6.11E-04 1.87E-04 0.000 lb/mmBtuO2 1.59E-07 1.56E-07 4.50E-08 0.000 mg/dscm 2.23E-04 2.14E-04 6.35E-05 0.000 mg/dscm@7%O2 1.84E-04 1.80E-04 5.23E-05 0.000 

### Compound: Chromium Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.00206 0.00416 0.00993 0.005 Elb/hr 1.15E-03 2.31E-03 1.69E-03 0.002 lb/mmBtuO2 2.97E-07 5.89E-07 4.07E-07 0.000 mg/dscm 4.17E-04 8.10E-04 5.73E-04 0.001



### Monday, February 14, 2011 Page 15 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 mg/dscm@7%O2 3.45E-04 6.83E-04 4.72E-04 0.001 

### Compound: Cobalt Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.029 0.00227 0.00252 0.011 Elb/hr 1.62E-02 1.26E-03 4.28E-04 0.006 lb/mmBtuO2 4.18E-06 3.21E-07 1.03E-07 0.000 mg/dscm 5.87E-03 4.42E-04 1.45E-04 0.002 mg/dscm@7%O2 4.85E-03 3.73E-04 1.19E-04 0.002 

### Compound: Filterable Particulate Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 4.2 2.5 2.5 3.067 Elb/hr 2.34E+00 1.39E+00 4.25E-01 1.385 lb/mmBtuO2 6.06E-04 3.54E-04 1.02E-04 0.000 mg/dscm 8.50E-01 4.87E-01 1.44E-01 0.494 mg/dscm@7%O2 7.02E-01 4.11E-01 1.19E-01 0.411 

### Compound: Lead Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.000653 0.0016 0.0022 0.001 Elb/hr 3.64E-04 8.88E-04 3.74E-04 0.001 lb/mmBtuO2 9.42E-08 2.26E-07 9.01E-08 0.000 mg/dscm 1.32E-04 3.12E-04 1.27E-04 0.000 mg/dscm@7%O2 1.09E-04 2.63E-04 1.05E-04 0.000 

### Compound: Manganese Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.00239 0.00677 0.00682 0.005 Elb/hr 1.33E-03 3.76E-03 1.16E-03 0.002 lb/mmBtuO2 3.45E-07 9.58E-07 2.79E-07 0.000 mg/dscm 4.84E-04 1.32E-03 3.93E-04 0.001 mg/dscm@7%O2 4.00E-04 1.11E-03 3.23E-04 0.001 

### Compound: Nickel Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.00663 0.0476 0.0511 0.035 Elb/hr 3.69E-03 2.64E-02 8.69E-03 0.013 lb/mmBtuO2 9.57E-07 6.74E-06 2.09E-06 0.000 mg/dscm 1.34E-03 9.27E-03 2.95E-03 0.005 mg/dscm@7%O2 1.11E-03 7.81E-03 2.43E-03 0.004 

### Compound: Selenium Average RunNumber PPE4-29-1 PPE4-29-2 PPE4-29-3 Mass_mg 0.02 0.0193 0.0211 0.020 Elb/hr 1.11E-02 1.07E-02 3.59E-03 0.008 lb/mmBtuO2 2.89E-06 2.73E-06 8.64E-07 0.000 mg/dscm 4.05E-03 3.76E-03 1.22E-03 0.003


### Monday, February 14, 2011 Page 16 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010

Process Run Data mg/dscm@7%O2 3.35E-03 3.17E-03 1.00E-03 0.003



### Location: PPE4 - PM - OTM - 27/28 Compound: Filterable Particulate Average RunNumber PPE4-27/28-2 PPE4-27/28-3 PPE4-27/28-1 Mass_mg 17.675 11.8 14.125 14.533 lb/mmBtuO2 1.15E-02 7.46E-03 3.62E-03 0.008 

### Compound: Filterable PM2.5 Average RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3 Mass_mg 12.6 17.15 7.275 12.342 lb/mmBtuO2 3.23E-03 1.12E-02 4.60E-03 0.006 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3 Mass_mg 2.727 12.199 30.602 15.176 lb/mmBtuO2 6.99E-04 7.94E-03 1.93E-02 0.009 

### Compound: Organic Condensible Particulate Average RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3 Mass_mg 4.05 3.55 21.85 9.817 lb/mmBtuO2 1.04E-03 2.31E-03 1.38E-02 0.006 

### Compound: Total Particulate Average RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3 Mass_mg 20.902 33.424 64.252 39.526 lb/mmBtuO2 5.36E-03 2.17E-02 4.06E-02 0.023 

### Compound: Total PM2.5 Average RunNumber PPE4-27/28-1 PPE4-27/28-2 PPE4-27/28-3 Mass_mg 19.377 32.899 59.727 37.334 lb/mmBtuO2 4.97E-03 2.14E-02 3.78E-02 0.021



### Monday, February 14, 2011 Page 17 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 Residual Oil (No. 6) Burned 28817 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/16/2010; Start - 09:28; End - 11:27 0



### 10Residual Oil (No. 6) Burned 28521 gal/hr Method 027/028; Run PM-1; Date - 3/16/2010; Start - 09:04; End - 15:00 0

11Residual Oil (No. 6) Burned 28287 gal/hr Method 027/028; Run PM-2; Date - 3/17/2010; Start - 20:11; End - 22:08 0

12Residual Oil (No. 6) Burned 27994 gal/hr Method 027/028; Run PM-3; Date - 3/18/2010; Start - 14:48; End - 16:56 0

2 Residual Oil (No. 6) Burned 28173 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/16/2010; Start - 15:00; End - 16:59 0

3 Residual Oil (No. 6) Burned 28217 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/16/2010; Start - 17:40; End - 19:39 0



### 4 Residual Oil (No. 6) Burned 28214 gal/hr Method 23; Run D/F-1; Date - 3/16/2010; Start - 12:30; End - 21:19 0

5 Residual Oil (No. 6) Burned 28375 gal/hr Method 23; Run D/F-2; Date - 3/17/2010; Start - 13:43; End - 22:20 0

6 Residual Oil (No. 6) Burned 28067 gal/hr Method 23; Run D/F-3; Date - 3/18/2010; Start - 12:28; End - 20:48 0

7 Residual Oil (No. 6) Burned 28199 gal/hr Method 29; Run M-1; Date - 3/16/2010; Start - 15:30; End - 20:02 0



### Monday, February 14, 2011 Page 18 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 8 Residual Oil (No. 6) Burned 28404 gal/hr Method 29; Run M-2; Date - 3/17/2010; Start - 14:30; End - 19:10 0

9 Residual Oil (No. 6) Burned 28141 gal/hr Method 29; Run M-3; Date - 3/18/2010; Start - 09:00; End - 13:37 0

1 Average Heat Input 3559 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/16/2010; Start - 09:28; End - 11:27 0



### 10Average Heat Input 3523 MMBtu/hr Method 027/028; Run PM-1; Date - 3/16/2010; Start - 09:04; End - 15:00 0

11Average Heat Input 3495 MMBtu/hr Method 027/028; Run PM-2; Date - 3/17/2010; Start - 20:11; End - 22:08 0

12Average Heat Input 3458 MMBtu/hr Method 027/028; Run PM-3; Date - 3/18/2010; Start - 14:48; End - 16:56 0

2 Average Heat Input 3480 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/16/2010; Start - 15:00; End - 16:59 0

3 Average Heat Input 3485 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/16/2010; Start - 17:40; End - 19:39 0



### 4 Average Heat Input 3484 MMBtu/hr Method 23; Run D/F-1; Date - 3/16/2010; Start - 12:30; End - 21:19 0

5 Average Heat Input 3505 MMBtu/hr Method 23; Run D/F-2; Date - 3/17/2010; Start - 13:43; End - 22:20 0

6 Average Heat Input 3466 MMBtu/hr Method 23; Run D/F-3; Date - 3/18/2010; Start - 12:28; End - 20:48 0



### Monday, February 14, 2011 Page 19 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 7 Average Heat Input 3483 MMBtu/hr Method 29; Run M-1; Date - 3/16/2010; Start - 15:30; End - 20:02 0

8 Average Heat Input 3509 MMBtu/hr Method 29; Run M-2; Date - 3/17/2010; Start - 14:30; End - 19:10 0

9 Average Heat Input 3476 MMBtu/hr Method 29; Run M-3; Date - 3/18/2010; Start - 09:00; End - 13:37 0

1 Steam Output 2372 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/16/2010; Start - 09:28; End - 11:27 0



### 10Steam Output 2359 1000 lb Method 027/028; Run PM-1; Date - 3/16/2010; Start - 09:04; End - 15:00 0

11Steam Output 2355 1000 lb Method 027/028; Run PM-2; Date - 3/17/2010; Start - 20:11; End - 22:08 0

12Steam Output 2352 1000 lb Method 027/028; Run PM-3; Date - 3/18/2010; Start - 14:48; End - 16:56 0

2 Steam Output 2340 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/16/2010; Start - 15:00; End - 16:59 0

3 Steam Output 2345 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/16/2010; Start - 17:40; End - 19:39 0

4 Steam Output 2344 1000 lb Method 23; Run D/F-1; Date - 3/16/2010; Start - 12:30; End - 21:19 0

5 Steam Output 2371 1000 lb Method 23; Run D/F-2; Date - 3/17/2010; Start - 13:43; End - 22:20 0



### Monday, February 14, 2011 Page 20 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 6 Steam Output 2352 1000 lb Method 23; Run D/F-3; Date - 3/18/2010; Start - 12:28; End - 20:48 0

7 Steam Output 2343 1000 lb Method 29; Run M-1; Date - 3/16/2010; Start - 15:30; End - 20:02 0

8 Steam Output 2379 1000 lb Method 29; Run M-2; Date - 3/17/2010; Start - 14:30; End - 19:10 0

9 Steam Output 2365 1000 lb Method 29; Run M-3; Date - 3/18/2010; Start - 09:00; End - 13:37 0

1 Unit Gross Electrical Output 377 MWg Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/16/2010; Start - 09:28; End - 11:27 0



### 10Unit Gross Electrical Output 377 MWg Method 027/028; Run PM-1; Date - 3/16/2010; Start - 09:04; End - 15:00 0

11Unit Gross Electrical Output 378 MWg Method 027/028; Run PM-2; Date - 3/17/2010; Start - 20:11; End - 22:08 0

12Unit Gross Electrical Output 376 MWg Method 027/028; Run PM-3; Date - 3/18/2010; Start - 14:48; End - 16:56 0

2 Unit Gross Electrical Output 377 MWg Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/16/2010; Start - 15:00; End - 16:59 0

3 Unit Gross Electrical Output 377 MWg Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/16/2010; Start - 17:40; End - 19:39 0

4 Unit Gross Electrical Output 377 MWg Method 23; Run D/F-1; Date - 3/16/2010; Start - 12:30; End - 21:19 0



### Monday, February 14, 2011 Page 21 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 5 Unit Gross Electrical Output 380 MWg Method 23; Run D/F-2; Date - 3/17/2010; Start - 13:43; End - 22:20 0

6 Unit Gross Electrical Output 377 MWg Method 23; Run D/F-3; Date - 3/18/2010; Start - 12:28; End - 20:48 0

7 Unit Gross Electrical Output 377 MWg Method 29; Run M-1; Date - 3/16/2010; Start - 15:30; End - 20:02 0

8 Unit Gross Electrical Output 381 MWg Method 29; Run M-2; Date - 3/17/2010; Start - 14:30; End - 19:10 0

9 Unit Gross Electrical Output 377 MWg Method 29; Run M-3; Date - 3/18/2010; Start - 09:00; End - 13:37 0

1 Unit Net Electric Generation 366 MWn Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/16/2010; Start - 09:28; End - 11:27 0



### 10Unit Net Electric Generation 366 MWn Method 027/028; Run PM-1; Date - 3/16/2010; Start - 09:04; End - 15:00 0

11Unit Net Electric Generation 366 MWn Method 027/028; Run PM-2; Date - 3/17/2010; Start - 20:11; End - 22:08 0

12Unit Net Electric Generation 365 MWn Method 027/028; Run PM-3; Date - 3/18/2010; Start - 14:48; End - 16:56 0

2 Unit Net Electric Generation 365 MWn Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/16/2010; Start - 15:00; End - 16:59 0

3 Unit Net Electric Generation 365 MWn Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/16/2010; Start - 17:40; End - 19:39 0



### Monday, February 14, 2011 Page 22 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010

APCD Run Data

Process Lab Run Data 4 Unit Net Electric Generation 365 MWn Method 23; Run D/F-1; Date - 3/16/2010; Start - 12:30; End - 21:19 0

5 Unit Net Electric Generation 368 MWn Method 23; Run D/F-2; Date - 3/17/2010; Start - 13:43; End - 22:20 0

6 Unit Net Electric Generation 365 MWn Method 23; Run D/F-3; Date - 3/18/2010; Start - 12:28; End - 20:48 0

7 Unit Net Electric Generation 365 MWn Method 29; Run M-1; Date - 3/16/2010; Start - 15:30; End - 20:02 0

8 Unit Net Electric Generation 369 MWn Method 29; Run M-2; Date - 3/17/2010; Start - 14:30; End - 19:10 0

9 Unit Net Electric Generation 366 MWn Method 29; Run M-3; Date - 3/18/2010; Start - 09:00; End - 13:37 0



### Run Name Value UOM Comments Target Value 1 LOW NOX BURNERS 477NOx Emissions 0


### 2 LOW NOX BURNERS 452NOx Emissions 0
3 LOW NOX BURNERS 449NOx Emissions 0
1 ELECTROSTATIC PRECIPITATORS 3.4 Opacity 0


### 2 ELECTROSTATIC PRECIPITATORS 3.4 Opacity 0
3 ELECTROSTATIC PRECIPITATORS 3.3 Opacity 0

Run Name ValueUOM Comments 

### 1 Fuel Higher Heating Value 18100Btu/lb 1 Fuel Moisture 0.807 % 1 Fuel Mercury Content 0.001 mg/kg 1 Fuel Chlorine Content 120 mg/kg 

### 1 Fuel Fluorine Content 78 mg/kg 1 Fuel Antimony Content 1.1 mg/kg 1 Fuel Arsenic Content 0.049 mg/kg 

### 1 Fuel Beryllium Content 0.008 mg/kg
Monday, February 14, 2011 Page 23 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 1 Fuel Cadmium Content 0.009 mg/kg 

### 1 Fuel Chromium Content 0.098 mg/kg 1 Fuel Cobalt Content 1.1 mg/kg 1 Fuel Lead Content 0.21 mg/kg 1 Fuel Manganese Content 0.5 mg/kg 

### 1 Fuel Nickel Content 23.6 mg/kg 1 Fuel Selenium Content 0.022 mg/kg 1 Fuel Sulfur Content 9760 mg/kg 

### 1 Fuel Proximate Analysis (Carbon) 88.7 % 1 Fuel Proximate Analysis (Hydrogen) 10.16 % 1 Fuel Proximate Analysis (Nitrogen) 0.54 % 1 Fuel Proximate Analysis (Oxygen) 0.5 % 

### 1 Fuel Proximate Analysis (Sulfur) 1.07 % 2 Fuel Higher Heating Value 18200Btu/lb 2 Fuel Moisture 2.08 % 

### 2 Fuel Mercury Content 0.001 mg/kg 2 Fuel Chlorine Content 140 mg/kg 2 Fuel Fluorine Content 65 mg/kg 2 Fuel Antimony Content 0.9 mg/kg 

### 2 Fuel Arsenic Content 0.053 mg/kg 2 Fuel Beryllium Content 0.008 mg/kg 2 Fuel Cadmium Content 0.009 mg/kg 

### 2 Fuel Chromium Content 0.092 mg/kg 2 Fuel Cobalt Content 1.1 mg/kg 2 Fuel Lead Content 0.2 mg/kg 2 Fuel Manganese Content 0.4 mg/kg 

### 2 Fuel Nickel Content 23.4 mg/kg 2 Fuel Selenium Content 0.022 mg/kg 2 Fuel Sulfur Content 9500 mg/kg 

### 2 Fuel Proximate Analysis (Carbon) 88.31 % 2 Fuel Proximate Analysis (Hydrogen) 9.96 % 2 Fuel Proximate Analysis (Nitrogen) 0.53 % 2 Fuel Proximate Analysis (Oxygen) 0.5 % 

### 2 Fuel Proximate Analysis (Sulfur) 1.06 % 3 Fuel Higher Heating Value 18200Btu/lb 3 Fuel Moisture 0.917 % 

### 3 Fuel Mercury Content 0.001 mg/kg 3 Fuel Chlorine Content 120 mg/kg 3 Fuel Fluorine Content 78 mg/kg 3 Fuel Antimony Content 0.9 mg/kg 

### 3 Fuel Arsenic Content 0.052 mg/kg 3 Fuel Beryllium Content 0.008 mg/kg 3 Fuel Cadmium Content 0.01 mg/kg



### Monday, February 14, 2011 Page 24 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 3 Fuel Chromium Content 0.091 mg/kg 

### 3 Fuel Cobalt Content 1.2 mg/kg 3 Fuel Lead Content 0.21 mg/kg 3 Fuel Manganese Content 0.4 mg/kg 3 Fuel Nickel Content 24.9 mg/kg 

### 3 Fuel Selenium Content 0.022 mg/kg 3 Fuel Sulfur Content 9680 mg/kg 3 Fuel Proximate Analysis (Carbon) 87.94 % 

### 3 Fuel Proximate Analysis (Hydrogen) 10.25 % 3 Fuel Proximate Analysis (Nitrogen) 0.55 % 3 Fuel Proximate Analysis (Oxygen) 0.5 % 3 Fuel Proximate Analysis (Sulfur) 1.07 %



### Monday, February 14, 2011 Page 25 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010 Sampling / Stack Data Results Detail


### Location PPE4 - D/F - Method 23 Average Run Number PPE4-23-1 PPE4-23-2 PPE4-23-3 Test Date 3/16/2010 3/17/2010 3/18/2010 Run Start Time 12:30:00 PM 1:43:00 PM12:28:00 PM Run Finish Time 8:30:00 PM9:43:00 PM 8:28:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.25 0.25 0.25 0.250 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.979 0.979 0.979 0.979 Barometric Pressure, inches of Mercury 29.71 29.71 29.65 29.690 Average Orifice Meter Differential, inches H2O 1.89 1.96 1.90 1.917 Dry Gas Meter Volume Sampled, cubic feet 370.510 358.170 365.490 364.723 Average Dry Gas Meter Temperature, °F 78.73 69.85 78.21 75.597 Dry Gas Meter Volume Sampled, dscf 354.661 348.655 349.498 350.938 Total Moisture Liquid collected, g 728 771 705.1 734.700 Volume of Water Vapor, standard cubic feet 34.27 36.29 33.19 34.583 Moisture Content of Stack Gas, % 8.81 9.43 8.67 8.970 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9119 0.9057 0.9133 0.910 Carbon Dioxide, % 14 13.9 14.04 13.980 Oxygen, % 4.08 4.41 4.01 4.167 Carbon Monoxide & Nitrogen, % 81.92 81.69 81.95 81.853 Fuel Factor 1.20 1.19 1.20 Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403 Wet Molecular weight, lb/lb-Mole 29.31 29.23 29.33 29.290 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.78 29.78 29.72 29.760 Average Stack Gas Temperature, °F 314.83 320.83 318.13 317.930 Average Velocity Head, inches of H2O 0.7828981180 585490.779615199

4743940.751870450

466923 0.771
Average Stack Gas Velocity, feet/second 59.87 60.05 58.83 59.583 Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617 Dry Volumetric Flow Rate, dry scfm 763,436.6 754,681.7 746,633.0754,917.100 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,234,341.0 1,238,052.1 1,212,899.31,228,430.8 00 Percent Isokinetic of Sampling Rate, % 97.6 97.0 98.3 97.633 Percent Excess Air, % 23.3 25.7 22.8 23.933 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 251 251 251 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 26 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 10 Average Run Number 4-CO-1 4-CO-2 4-CO-3 Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Analyzer Make THERMO THERMO THERMO Analyzer Model 48i 48i 48i Analyzer Serial Number INST-CO0017 INST-CO0017 INST-CO0017 Operating Range 9.2 9.2 9.2 9.200 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 5 5 5 5.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 0.23 0.25 0.27 0.250 Calibration Pre Zero Cylinder Bias 2.72 2.93 3.15 2.933 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID AL1933 AL1933 AL1933 Calibration Pre High Cylinder Instrument Response 4.85 4.87 4.99 4.903 Calibration Pre High Cylinder Bias 0.22 0.43 1.74 0.797 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 0.25 0.27 0.28 0.267 Calibration Post Zero Cylinder Bias 2.93 3.15 3.26 3.113 Calibration Post Zero Cylinder Drift 0.21 0.22 0.11 0.180 Calibration Post High Cylinder ID AL1933 AL1933 AL1933 Calibration Post High Cylinder Instrument Response 4.87 4.99 5.27 5.043 Calibration Post High Cylinder Bias 0.43 1.74 4.78 2.317 Calibration Post High Cylinder Drift 0.21 1.31 3.04 1.520 Cavg 5.43 2.51 2.71 3.550 Cavg Units ppmvd ppmvd ppmvd Cgas 5.527 2.3704 2.4676 3.455 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 27 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 25A Average Run Number 4-THC-1 4-THC-2 4-THC-3 Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Analyzer Make VIG VIG VIG Analyzer Model 20 20 20 20.000 Analyzer Serial Number INST-TH0007 INST-TH0007 INST-TH0007 Operating Range 50 50 50 50.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 6 6 6 6.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 0 0.73 1.54 0.757 Calibration Pre Zero Cylinder Bias -0.14 1.32 2.94 1.373 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID CC115743 CC115743 CC115743 Calibration Pre High Cylinder Instrument Response 14.18 15.01 15.07 14.753 Calibration Pre High Cylinder Bias -0.58 1.08 1.2 0.567 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 0.73 1.54 1.3 1.190 Calibration Post Zero Cylinder Bias 1.32 2.94 2.46 2.240 Calibration Post Zero Cylinder Drift 1.46 1.62 0.48 1.187 Calibration Post High Cylinder ID CC115743 CC115743 CC115743 Calibration Post High Cylinder Instrument Response 15.01 15.07 15.13 15.070 Calibration Post High Cylinder Bias 1.08 1.2 1.32 1.200 Calibration Post High Cylinder Drift 1.66 0.12 0.12 0.633 Cavg 1.06 1.85 1.43 1.447 Cavg Units ppmvw ppmvw ppmvw Cgas 0.7713 0.8121 0.0115 0.532 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0.7033028812 368240.740453074

4336571.052631578

94737E-02 0.485
Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 28 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 3A CO2 Average Run Number 4-CO2-1 4-CO2-2 4-CO2-3 Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Analyzer Make THERMO THERMO THERMO Analyzer Model 410i 410i 410i Analyzer Serial Number INST-C2-0010 INST-C2- 0010 INST-C2-

0010 Operating Range 19.3 19.3 19.3 19.300 Operating Units % % % No. Readings/Avg. 240 240 240 240.000 Calibration Set 2 2 2 2.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 0.14 0.12 0.18 0.147 Calibration Pre Zero Cylinder Bias 0.62 0.52 0.83 0.657 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID AAL12025- CO2AAL12025-

CO2 AAL12025-

CO2 Calibration Pre High Cylinder Instrument Response 8.94 8.88 9.01 8.943 Calibration Pre High Cylinder Bias 0.1 -0.21 0.47 0.120 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 0.12 0.18 0.43 0.243 Calibration Post Zero Cylinder Bias 0.52 0.83 2.12 1.157 Calibration Post Zero Cylinder Drift 0.1 0.31 1.29 0.567 Calibration Post High Cylinder ID AAL12025- CO2AAL12025-

CO2 AAL12025-

CO2 Calibration Post High Cylinder Instrument Response 8.88 9.01 9.4 9.097 Calibration Post High Cylinder Bias -0.21 0.47 2.49 0.917 Calibration Post High Cylinder Drift 0.31 0.68 2.02 1.003 Cavg 14 13.95 14.31 14.087 Cavg Units %vd %vd %vd Cgas 14.0438 13.9491 13.9893 13.994 Cgas Units %vd %vd %vd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units %vw %vw %vw



### Monday, February 14, 2011 Page 29 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 3A O2 Average Run Number 4-O2-1 4-O2-2 4-O2-3 Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Analyzer Make THERMO THERMO THERMO Analyzer Model 42i-HL 42i-HL 42i-HL Analyzer Serial Number INST-N2-0002 INST-N2- 0002 INST-N2-

0002 Operating Range 21.1 21.1 21.1 21.100 Operating Units % % % No. Readings/Avg. 240 240 240 240.000 Calibration Set 1 1 1 1.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 0.01 0.12 -0.08 0.017 Calibration Pre Zero Cylinder Bias 0.05 0.57 -0.38 0.080 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID AAL12025-O2AAL12025- O2 AAL12025-

O2 Calibration Pre High Cylinder Instrument Response 12.02 11.99 11.87 11.960 Calibration Pre High Cylinder Bias -0.33 -0.47 -1.04 -0.613 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 0.12 -0.08 0 0.013 Calibration Post Zero Cylinder Bias 0.57 -0.38 0 0.063 Calibration Post Zero Cylinder Drift 0.52 0.95 0.38 0.617 Calibration Post High Cylinder ID AAL12025-O2AAL12025- O2 AAL12025-

O2 Calibration Post High Cylinder Instrument Response 11.99 11.87 11.95 11.937 Calibration Post High Cylinder Bias -0.47 -1.04 -0.66 -0.723 Calibration Post High Cylinder Drift 0.14 0.57 0.38 0.363 Cavg 4.18 3.99 3.94 4.037 Cavg Units %vd %vd %vd Cgas 4.1701 4.0333 4.03 4.078 Cgas Units %vd %vd %vd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units %vw %vw %vw



### Monday, February 14, 2011 Page 30 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 6C Average Run Number 4-SO2-1 4-SO2-2 4-SO2-3 Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Analyzer Make THERMO THERMO THERMO Analyzer Model 43i-HL 43i-HL 43i-HL Analyzer Serial Number INST-S2-0005 INST-S2- 0005 INST-S2-

0005 Operating Range 959 959 959 959.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 3 3 3 3.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 6.7 5.07 8.8 6.857 Calibration Pre Zero Cylinder Bias 0.69 0.52 0.91 0.707 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID CC66246 CC66246 CC66246 Calibration Pre High Cylinder Instrument Response 412 417 422 417.000 Calibration Pre High Cylinder Bias -2.35 -1.82 -1.3 -1.823 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 5.07 8.8 9.02 7.630 Calibration Post Zero Cylinder Bias 0.52 0.91 0.93 0.787 Calibration Post Zero Cylinder Drift 0.17 0.39 0.02 0.193 Calibration Post High Cylinder ID CC66246 CC66246 CC66246 Calibration Post High Cylinder Instrument Response 417 422 422 420.333 Calibration Post High Cylinder Bias -1.82 -1.3 -1.3 -1.473 Calibration Post High Cylinder Drift 0.53 0.52 0 0.350 Cavg 524.96 537.14 532.18 531.427 Cavg Units ppmvd ppmvd ppmvd Cgas 543.7003 550.0412 542.1568 545.299 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 31 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Gases - Method 7E Average Run Number 4-NOx-1 4-NOx-2 4-NOx-3 Test Date 3/16/2010 3/16/2010 3/16/2010 Run Start Time 9:28:19 AM3:00:03 PM 5:40:03 PM Run Finish Time 11:27:49 AM4:59:33 PM 7:39:33 PM Carbon Dioxide, % 14.04 13.95 13.99 13.993 Oxygen, % 4.17 4.03 4.03 4.077 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 765731 765731 765731765,731.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.82 8.82 8.82 8.820 Analyzer Make THERMO THERMO THERMO Analyzer Model 42i-HL 42i-HL 42i-HL Analyzer Serial Number INST-N2-0002 INST-N2- 0002 INST-N2-

0002 Operating Range 1110 1110 1110 1,110.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 4 4 4 4.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 1.23 7.73 10.87 6.610 Calibration Pre Zero Cylinder Bias 0.05 0.64 0.92 0.537 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID ALM042523ALM042523ALM042523 Calibration Pre High Cylinder Instrument Response 543 537 536.88 538.960 Calibration Pre High Cylinder Bias -1.09 -1.63 -1.64 -1.453 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 7.73 10.87 13.14 10.580 Calibration Post Zero Cylinder Bias 0.64 0.92 1.12 0.893 Calibration Post Zero Cylinder Drift 0.59 0.28 0.2 0.357 Calibration Post High Cylinder ID ALM042523ALM042523ALM042523 Calibration Post High Cylinder Instrument Response 537 536.88 543 538.960 Calibration Post High Cylinder Bias -1.63 -1.64 -1.09 -1.453 Calibration Post High Cylinder Drift 0.54 0.01 0.55 0.367 Cavg 498.4 498.15 491.64 496.063 Cavg Units ppmvd ppmvd ppmvd Cgas 504.5082 506.7867 496.9558 502.750 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 32 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - Metals - Method 29 Average Run Number PPE4-29-1 PPE4-29-2 PPE4-29-3 Test Date 3/16/2010 3/17/2010 3/18/2010 Run Start Time 3:30:00 PM2:30:00 PM 9:00:00 AM Run Finish Time 7:30:00 PM6:30:00 PM 1:00:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 240 240 240 Nozzle Diameter, inches 0.25 0.25 0.25 0.250 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.002 0.987 0.987 0.992 Barometric Pressure, inches of Mercury 29.71 29.65 29.62 29.660 Average Orifice Meter Differential, inches H2O 1.83 2.03 1.93 1.930 Dry Gas Meter Volume Sampled, cubic feet 178.370 187.590 624.640 330.200 Average Dry Gas Meter Temperature, °F 79.46 76.75 68.90 75.037 Dry Gas Meter Volume Sampled, dscf 174.489 181.398 612.219 322.702 Total Moisture Liquid collected, g 387.8 426.6 403.7 406.033 Volume of Water Vapor, standard cubic feet 18.25 20.08 19.00 19.110 Moisture Content of Stack Gas, % 9.47 9.97 3.01 7.483 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9053 0.9003 0.9699 0.925 Carbon Dioxide, % 14 13.9 14.04 13.980 Oxygen, % 4.08 4.41 4.01 4.167 Carbon Monoxide & Nitrogen, % 81.92 81.69 81.95 81.853 Fuel Factor 1.20 1.19 1.20 Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403 Wet Molecular weight, lb/lb-Mole 29.23 29.16 30.04 29.477 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.78 29.72 29.69 29.730 Average Stack Gas Temperature, °F 316.21 319.50 319.50 318.403 Average Velocity Head, inches of H2O 0.7353081038 275220.801331824

3646150.760726953

506861 0.766
Average Stack Gas Velocity, feet/second 58.15 60.97 58.55 59.223 Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617 Dry Volumetric Flow Rate, dry scfm 734,828.4 761,437.7 786,948.2761,071.433 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,198,879.7 1,257,019.7 1,207,126.51,221,008.6 33 Percent Isokinetic of Sampling Rate, % 99.7 100.1 326.8 175.533 Percent Excess Air, % 23.3 25.7 22.8 23.933 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 251 251 251 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 33 of 34

### Port Everglades Energy Center, Unit #4, Information Collection Request
6/10/2010
Location PPE4 - PM - OTM - 27/28 Average Run Number PPE4-27/28-1PPE4-27/28- 2PPE4-27/28-3

Test Date 3/16/2010 3/17/2010 3/18/2010 Run Start Time 9:04:00 AM8:11:00 PM 2:48:00 PM Run Finish Time 3:00:00 PM10:08:00 PM 4:56:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 288 118 120 Nozzle Diameter, inches 0.172 0.172 0.172 0.172 Pitot Tube Coefficient 0.8 0.8 0.8 0.800 Dry Gas Meter Calibration Factor 1.002 0.987 0.987 0.992 Barometric Pressure, inches of Mercury 29.74 29.7 29.65 29.697 Average Orifice Meter Differential, inches H2O 0.39 0.40 0.40 0.397 Dry Gas Meter Volume Sampled, cubic feet 99.510 40.880 40.900 60.430 Average Dry Gas Meter Temperature, °F 73.17 76.29 73.04 74.167 Dry Gas Meter Volume Sampled, dscf 98.243 39.472 39.665 59.127 Total Moisture Liquid collected, g 188.7 85.2 75.2 116.367 Volume of Water Vapor, standard cubic feet 8.88 4.01 3.54 5.477 Moisture Content of Stack Gas, % 8.29 9.22 8.19 8.567 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9171 0.9078 0.9181 0.914 Carbon Dioxide, % 14 13.9 14.04 13.980 Oxygen, % 4.08 4.41 4.01 4.167 Carbon Monoxide & Nitrogen, % 81.92 81.69 81.95 81.853 Fuel Factor 1.20 1.19 1.20 Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403 Wet Molecular weight, lb/lb-Mole 29.37 29.26 29.39 29.340 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.81 29.77 29.72 29.767 Average Stack Gas Temperature, °F 314.33 320.25 318.17 317.583 Average Velocity Head, inches of H2O 0.7998552239 025780.746789430

9987870.761009953

722415 0.769
Average Stack Gas Velocity, feet/second 57.52 55.94 56.31 56.590 Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617 Dry Volumetric Flow Rate, dry scfm 738,872.8 704,946.1 718,369.8720,729.567 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,185,891.0 1,153,316.1 1,160,944.41,166,717.1 67 Percent Isokinetic of Sampling Rate, % 98.3 101.1 98.0 99.133 Percent Excess Air, % 23.3 25.7 22.8 23.933 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 251 251 251 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 34 of 34