IT 2 

TANI(S 

If) 

;'I; 

~ n 

:I: 

..., 

N 

n 

0 

~ 

" 

7" 

=l 

(I) 

~ 

N 

-, 

n

0 Z t: t') 

~ 

~ Ii' 

~ ;rJ

,. 

~ 

-< 

-; 


B. EUOOI and EU002 - Tangential Coal Fired Units 1 & 2 

Condition(s) PollutantJParametcr Permit Limit Compliance Demonstration 

Method Frequency 

Reporting 

Requirements 

B. I, B.4, B.13, 

B.14, B.24, 

B.25, B.28, 

B.29, B.30, 

B.32 & B.33 

Opacity 200/.,127% 

COMS Ongoing Quarterly 

Method 9 As required by 

the Department 

and Section 

llI.A.1 

Semiannually 

B.2, B.15, 

B.24, B.28, 

B.29, B.32 & 

B.33 

PM 0.1 IblMMBtu Method 5 or 5B Annual 

B.3, B.4, B.5, 

B.17, B.18, 

B.19, B.24, 

B.26, B.28, 

B.29, B.32, 

B.33 

S02 1.2 IblMMBtu Method 6 or 6C Annual Semiannually 

CEMS Ongoing Quarterly 

B.3,B.4, B.5, 

B.7, B.16, 

B.18, B.19, 

B.24, B.26, 

B.28, B.29, 

B.32 & B.33 

NO, 0.7 IblMMBtu Method 7 or 7E Annual Semiannually 

CEMS Ongoing Quarterly 

0.40 Ib/MMBtu 

(annual average) 

40 CFR 72-78 

and Appendix H 

As required by 

Appendix H 

B.S, B.6, B.7, 

B.18, B.19, 

B.26, B.28, 

B.31 -B.33 

Acid Rain Provisions 40 CFR 72-78 and 

Appendix H 

40 CFR 72-78 

and Appendix H 

As required by 

Appendix H 

B.8, B.20, 

B27, B.28, 

B.32, B.33 

PM CAM Plan ARM 17.8.1506 Provisions from 

CAM Plan, 

Appendix I 

Ongoing 

B.9, B.21, 

B.28, B.32, 

B.33 

Syncoal1imit 700,800 tonsll2­

month rolling 

Log Ongoing Semiannually 

B.IO, B.22, 

B.28, B.32 & 

B.33 

Petroleum coke limit 280,320 tonsll2­

month rolling 

Log Ongoing 

B.II, B.22, 

B.28 , B.32 & 

B.33 

Petroleum coke limit 28% of maximum 

heat input value 

Log Ongoing 

B.12, B.23, 

B.28, B.32, 

B.33 

Scrubbers Maintain & Operate Log Daily 

Conditions 

8.1, 	 PPL shall not cause or authorize to be discharged into the atmosphere from Units 1 & 2 any 

visible emissions that exhibit an opacity of20% or greater averaged over 6 consecutive minutes 

except for one 6-minute period per hour of not greater than 27% opacity (ARM 17.8.340 and 40 

CFR 60, Subpart D). 

B.2. 	 PPL shall not cause to be discharged into the atmosphere PM in excess of 0.1 0 IbIMMBtu, as 

averaged over 3 hours (minimum) of reference method testing (40 CFR §S2.21 , ARM 17.8.340, 

and 40 CFR 60, Subpart D). 

B.3. 	 Any gaseous e'missions discharged into the atmosphere shall not exceed 1.2 IblMMBtu Sulfur 

Dioxide (S02) and 0.7 Ib/MMBtu NO, (ARM 17.8.340 and 40 CFR 60, Subpart D). 

OP0513-07 	 7 Draft : 05 / 17/20 II 
C. EU003 and EU004 - Tangential Coal Fired Units 3 & 4 

Condition(s) PollutantiParameter Permit Limit Compliance Demonstration 

Method Frequency 

Reporting 

Requirements 

C.I, C.21, C.24, 

C.25. C.36, 

C.4I, C.42. 

C.45. C.47­

C.50 

Opacity 200/.,127% COMS Ongoing Quarterly 

Method 9 As required by the 

Department and 

Section IlIAI 

Semiannually 

C.2, C.3, C.4, 

C.26, C.42, C.47 

- C.49 

PM 0.05 IblMMBtu Method 5 or 

Method 5B 

Annual 

3791blhr 

O.IOlbIMMBtu 

C.4-C.8,C.21, 

C.27, C.28, 

C.36, C.42, 

C.43, C.45, C.47 

-C.50 

S02 1.2 IblMMBtu Method 6 or 6C Annual 

0.181b1MMBtu 

(calendar day 

average) 

CEMS Ongoing Quarterly 

761 Iblhr (30 day 

roll ing average) 

1363 Iblhr 

(calendar day 

average) 

4140 Iblhr (3-hr 

rolling average) 

C.9, C.29, C.38, 

C.42, C.47­

C.50 

% sulfur I% sulfur content 

of coal 

Composite coal 

samples in 

accordance with 

Method 19 

Ongoing Semiannually 

C.4, C.IO, C.II, 

C.12, C.21, 

C.30, C.31, 

c.32, C.36, 

C.39, C.42, 

C.43, C.45, 

C.47-C.50 

NO, 0.71b1MMBtu Method 7 or 7E Annual 

CEMS Ongoing Quarterly 

5301 Iblhr 

0.40 IblMMBtu 

(annual average) 

40 CFR 72-78 

and Appendix H 

As required by 

Appendix H 

E=0.2x+0.3y=O.7z 

x+y+z 

Emissions limit 

calculations 

When burning fuel 

other than coal 

Semiannually 

C.13,C.31, 

C36, C.43, 

C.45, C.47­

C.50 

N02 0.71b1MMBtu 

(calendar day 

average) 

CEMS Ongoing Quarterly 

CI4,C.17, 

C.31, C.36, 

C.43, C.45, 

C.47- C.50 

NO, (30-day rolling 

average) 

0.18 Ib/MMBtu if 

unit operating> 

400MW 

CEMS Ongoing 

0.30 IblMMBtu if 

unit operating 

=<400 MW 

1,363 Iblhr 

NO, (24-hour average) 0.25 IblMMBtu if 

unit operating> 

400MW 

0.30 IblMMBtu if 

unit operating 

=<400 MW 

1,893 Iblhr 

C.IS, C.16, 

C.33, C.40, CA7 

- CA9 

NO, Control Operate digital 

controls, low-NO, 

burners, overfire 

air 

Documentation Ongoing Semiannually 

C.18, C.33, 

CAO, CA7­

C.49 

NO, Control Classification, 

BART, visibility, 

and Baseline 

Visibility 

As required by 

EPA 

As required by 

EPA 

As required by. 

EPA 

C.19, C.20, 

C.34, CA3, 

C.44, CA7-C49 

Acid Rain Provisions 40 CFR 72-78 and 

Appendix H 

40 CFR 72-78 

and Appendix H 

As required by 

Appendix H 

Quarterly 

OP0513-07 12 Draft: 05/1712011