## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit Category/Subcategory**  **Run # Method used**  **(26 or 26A) Sample time** 

**(min.) Sample volume** 

**(dscf) Percent H2O** 

**(Bws) Mass Cl2** 

**(ug) Mass HF** 

**(ug) Mass HCL** 

**(ug) ppm** **lb/hr lb/MMBtu** **ppm @ 7% O2**  AKDoyonUtilities_AK/4 Solid/Coal/Stoker 4 26A 60 420 6500 0.662 3.50E-03 AKDoyonUtilities_AK/4 Solid/Coal/Stoker 5 26A 60 400 6200 0.626 3.20E-03 AKDoyonUtilities_AK/4 Solid/Coal/Stoker 6 26A 60 410 5800 0.591 3.10E-03 AKDoyonUtilities_AK/7 Solid/Coal/Stoker 1 26A 60 430 5100 0.526 2.80E-03 AKDoyonUtilities_AK/7 Solid/Coal/Stoker 2 26A 60 550 5000 0.515 2.90E-03 AKDoyonUtilities_AK/7 Solid/Coal/Stoker 3 26A 60 480 5500 0.568 3.40E-03 IAMuscatinePowerandWater/7 Solid/Coal/Stoker 1 26 60 4.19 203 402 2.060.421 5.50E-03 IAMuscatinePowerandWater/7 Solid/Coal/Stoker 2 26 60 4.32 237 320 1.720.6754.20E-03 IAMuscatinePowerandWater/7 Solid/Coal/Stoker 3 26 60 4.30 255 297 2.520.621 3.70E-03

IDAmalgamatedSugarCoTwinFalls Solid/Coal/PC 1 26 60 4.33 200 206 1.240.432 2.00E-03 IDAmalgamatedSugarCoTwinFalls Solid/Coal/PC 2 26 60 3.93 67 69 0.480.164 1.00E-03 IDAmalgamatedSugarCoTwinFalls Solid/Coal/PC 3 26 60 3.97 100 103 0.7140.248 1.00E-03 IDTASCOPaul/B&W Boiler Solid/Coal/Stoker 1 26A 64 38.29 40 <0.025<0.0082 IDTASCOPaul/B&W Boiler Solid/Coal/Stoker 2 26A 64 43.52 42 <0.023<0.0088 IDTASCOPaul/B&W Boiler Solid/Coal/Stoker 3 26A 64 43.26 39 <0.022<0.0082 ILPrairiePowerPearl/B1 Solid/Coal/PC 1 26A 60 49.51 0.07 3190 1.5 0.58 2.00E-03 ILPrairiePowerPearl/B1 Solid/Coal/PC 2 26A 60 49.91 0.062 3080 1.440.56561.90E-03 ILPrairiePowerPearl/B1 Solid/Coal/PC 3 26A 60 49.92 0.071 2970 1.380.54271.90E-03 INSABICInnovativePlastics/09-002 06-27-06 Solid/Coal/Stoker 1 26 60 4.16 0.088 2.331.186 3.30E-03 INSABICInnovativePlastics/09-002 06-27-06 Solid/Coal/Stoker 2 26 60 4.07 0.077 3.661.866 5.50E-03 INSABICInnovativePlastics/09-002 06-27-06 Solid/Coal/Stoker 3 26 60 4.23 0.077 3.9 1.9545.90E-03 INSABICInnovativePlastics/09-002 04-6-2005 Solid/Coal/Stoker 1 26 60 4.16 0.088 0.368 2.061.089 3.00E-03 INSABICInnovativePlastics/09-002 04-6-2005 Solid/Coal/Stoker 2 26 60 4.14 0.077 0.203 1.140.607 2.00E-03 INSABICInnovativePlastics/09-002 04-6-2005 Solid/Coal/Stoker 3 26 60 4.23 0.077 0.355 1.951.046 3.00E-03 LAGPPortHudson/no.6 Solid/Biomass/FB 4 26A 60 46.05 0.1194 944 0.699 6.00E-04 LAGPPortHudson/no.6 Solid/Biomass/FB 5 26A 60 45.59 0.1186 1320 0.973 8.00E-04 LAGPPortHudson/no.6 Solid/Biomass/FB 6 26A 60 45.32 0.1105 1140 0.849 7.00E-04
MICityofEscanaba/EUBoiler no. 1 Solid/Coal/Stoker 4 26A 60 42.66 0.071 0.887 0.46 6.00E-04
MICityofEscanaba/EUBoiler no. 1 Solid/Coal/Stoker 5 26A 60 43.32 0.07 0.862 0.44 6.00E-04
MICityofEscanaba/EUBoiler no. 1 Solid/Coal/Stoker 6 26A 60 43.82 0.067 0.851 0.43 6.00E-04 MNAmericanCrystalMoorhead/Boiler 3 Solid/Coal/Stoker 1 26 60 46.37 1370 0.69 0.64 MNAmericanCrystalMoorhead/Boiler 3 Solid/Coal/Stoker 2 26 60 45.89 4350 2.2 2.07 MNAmericanCrystalMoorhead/Boiler 3 Solid/Coal/Stoker 3 26 60 45.39 3310 1.7 1.58 ALBoiseWhitePaperJackson Solid/Biomass/Stoker 1 26A 120 48.21 0.2290.103 3.00E-04 0.22 ALBoiseWhitePaperJackson Solid/Biomass/Stoker 2 26A 120 48.80 0.2460.110 3.00E-04 0.232 ALBoiseWhitePaperJackson Solid/Biomass/Stoker 3 26A 120 50.28 0.2340.109 3.00E-04 0.22 ALIPCourtlandNo. 3 Comb Blr Solid/Biomass/FB 1 26A 120 64.00 450 0.1830.136 3.06E-04 ALIPCourtlandNo. 3 Comb Blr Solid/Biomass/FB 2 26A 120 65.00 352 0.1260.105 2.37E-04 ALIPCourtlandNo. 3 Comb Blr Solid/Biomass/FB 3 26A 120 64.00 246 0.0890.075 1.67E-04 ARAnthonyForestProducts/SN-12 Solid/Biomass/Fuel Cell 1 26 120 0.203 0.14 2.10E-04 0.16 ARAnthonyForestProducts/SN-12 Solid/Biomass/Fuel Cell 2 26 120 0.206 0.16 2.30E-04 0.17 ARAnthonyForestProducts/SN-12 Solid/Biomass/Fuel Cell 3 26 120 0.215 0.11 1.60E-04 0.11
IARoquetteAmerica/Circulating Fluidized Bed Boiler (121)Solid/Coal/FB 1 26A 120 65.51 0.070.0708.00E-05 0.06
IARoquetteAmerica/Circulating Fluidized Bed Boiler (121)Solid/Coal/FB 2 26A 120 64.91 0.050.0607.00E-05 0.05
IARoquetteAmerica/Circulating Fluidized Bed Boiler (121)Solid/Coal/FB 3 26A 120 66.71 0.030.030 3.00E-05 0.02 MEBoralexStratton/Boiler #1 Solid/Biomass/Stoker 1 26A 60 42.40 0.088 0.1 MEBoralexStratton/Boiler #1 Solid/Biomass/Stoker 2 26A 60 42.60 0.088 0.1 MEBoralexStratton/Boiler #1 Solid/Biomass/Stoker 3 26A 60 42.20 0.086 0.1 MSHoodWaynesboro/AA-001 (wood-fired boiler) Solid/Biomass/Stoker 1 26A 60 37.28 0.2 0.030 2.80E-04 MSHoodWaynesboro/AA-001 (wood-fired boiler) Solid/Biomass/Stoker 2 26A 60 37.93 0.2 0.025 2.35E-04 MSHoodWaynesboro/AA-001 (wood-fired boiler) Solid/Biomass/Stoker 3 26A 60 40.90 0.1 0.013 1.18E-04 NCGPRoxboro/ES-1 Solid/Biomass/Stoker 1 26A 60 32.56 0.120.010 NCGPRoxboro/ES-1 Solid/Biomass/Stoker 2 26A 120 68.49 0.070.010 NCGPRoxboro/ES-1 Solid/Biomass/Stoker 3 26A 120 70.58 0.070.010 NDCargillWestFargo/Foster Wheeler Boiler (EU43) Solid/Biomass/FB 1 26A 120 52.26 794 0.350.024 NDCargillWestFargo/Foster Wheeler Boiler (EU43) Solid/Biomass/FB 2 26A 120 51.92 <226 <0.10<0.007 NDCargillWestFargo/Foster Wheeler Boiler (EU43) Solid/Biomass/FB 3 26A 120 52.19 <304 <0.14<0.009 NDMinnDakFarmers/Babcock and Wilcox Boiler #5 Solid/Coal/Stoker 1 26A 60 43.23 720 0.39 NDMinnDakFarmers/Babcock and Wilcox Boiler #5 Solid/Coal/Stoker 2 26A 60 42.56 390 0.21 NDMinnDakFarmers/Babcock and Wilcox Boiler #5 Solid/Coal/Stoker 3 26A 60 41.67 430 0.24 ORRoseburgCoquille/Boiler 1 Solid/Biomass/Stoker 1 26A 60 0.033 3.30E-04 ORRoseburgCoquille/Boiler 1 Solid/Biomass/Stoker 2 26A 60 0.041 3.83E-04 ORRoseburgCoquille/Boiler 1 Solid/Biomass/Stoker 3 26A 60 0.995 1.02E-02 ORRoseburgCoquille/Boiler 1 Solid/Biomass/Stoker 4 26A 60 1.141 1.13E-02 ORRoseburgCoquille/Boiler 1 Solid/Biomass/Stoker 5 26A 60 2.207 2.28E-02 ORRoseburgCoquille/Boiler 1 Solid/Biomass/Stoker 6 26A 60 4.520 5.23E-02 

### Reported Mass/Unit

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit Category/Subcategory**  **Run # Method used**  **(26 or 26A) Sample time** 

**(min.) Sample volume** 

**(dscf) Percent H2O** 

**(Bws) Mass Cl2** 

**(ug) Mass HF** 

**(ug) Mass HCL** 

**(ug) ppm** **lb/hr lb/MMBtu** **ppm @ 7% O2**  **Reported Mass/Unit**

ORRoseburgRiddle2/Boiler 2 Solid/Biomass/Stoker 1 26A 60 0.0294.20E-04 ORRoseburgRiddle2/Boiler 2 Solid/Biomass/Stoker 2 26A 60 0.025 5.20E-04 ORRoseburgRiddle2/Boiler 2 Solid/Biomass/Stoker 3 26A 60 0.049 8.60E-04

PADomtarJohnsonburg/#81 Coal Boiler Solid/Coal/PC 1 26A 60 41.16 0.4008.00E-04

PADomtarJohnsonburg/#81 Coal Boiler Solid/Coal/PC 2 26A 60 40.34 0.500 1.00E-03

PADomtarJohnsonburg/#81 Coal Boiler Solid/Coal/PC 3 26A 60 42.55 0.3007.00E-04

PADomtarJohnsonburg/#81 Coal Boiler Solid/Coal/PC 4 26A 60 41.35 1.300 1.20E-03

PADomtarJohnsonburg/#81 Coal Boiler Solid/Coal/PC 5 26A 60 42.30 1.000 1.00E-03

PADomtarJohnsonburg/#81 Coal Boiler Solid/Coal/PC 6 26A 60 43.05 1.100 1.10E-03 SCMarlboroPaper/hogged Fuel Boiler Solid/Biomass/Stoker 1 26A 180 <0.018<0.0001 SCMarlboroPaper/hogged Fuel Boiler Solid/Biomass/Stoker 2 26A 180 <0.019<0.0001 SCMarlboroPaper/hogged Fuel Boiler Solid/Biomass/Stoker 3 26A 180 <0.020<0.0001 TNBowaterNewsprint/Bubbling FB Boiler Solid/Biomass/FB 1 26A 120 85.85 0.33 4.30E-04 TNBowaterNewsprint/Bubbling FB Boiler Solid/Biomass/FB 2 26A 120 85.14 0.13 1.80E-04 TNBowaterNewsprint/Bubbling FB Boiler Solid/Biomass/FB 3 26A 120 84.50 0.52 7.10E-04 TNDomtar2384/HFB1-1 Solid/Biomass/FB 1 26A 120 86.18 0.195 1.94 2.70E-03 TNDomtar2384/HFB1-1 Solid/Biomass/FB 2 26A 120 85.28 0.211 2.45 3.40E-03 TNDomtar2384/HFB1-1 Solid/Biomass/FB 3 26A 120 88.65 0.192 2.26 3.20E-03 TNEastman_NO_CBIDATA/Boiler 30 Solid/Coal/FB 1 26A 120 84.81 0.136 <0.05 <7.30E-05 TNEastman_NO_CBIDATA/Boiler 30 Solid/Coal/FB 2 26A 120 84.87 0.14 <0.05 <7.30E-05 TNEastman_NO_CBIDATA/Boiler 30 Solid/Coal/FB 3 26A 120 87.42 0.129 <0.05 <7.10E-05 TNInvistaChattanoogaEU003 - Vaporizer 2 Liquid 1 26A 60 43.04 0.113 0.004 1.95E-04 0.47 TNInvistaChattanoogaEU003 - Vaporizer 2 Liquid 2 26A 60 42.57 0.118 0.004 2.09E-04 0.47 TNInvistaChattanoogaEU003 - Vaporizer 2 Liquid 3 26A 60 42.22 0.131 0.003 1.28E-04 0.48 VASmurfitStoneWestpt/PB08 Liquid 4 26A 60 37.70 0.900 VASmurfitStoneWestpt/PB08 Liquid 5 26A 60 36.73 1.000 VASmurfitStoneWestpt/PB08 Solid/Coal/PC 1 26A 120 84.67 7.40E-04 VASmurfitStoneWestpt/PB08 Solid/Coal/PC 2 26A 120 85.89 5.04E-04 VASmurfitStoneWestpt/PB08 Solid/Coal/PC 3 26A 120 85.20 7.62E-04 VAUniversityofVirginia/7103-1-01R Solid/Coal/Stoker 1 26A 120 87.75 <0.40<0.046<5.81E-04 VAUniversityofVirginia/7103-1-01R Solid/Coal/Stoker 2 26A 120 82.27 0.420.049 5.94E-04 VAUniversityofVirginia/7103-1-01R Solid/Coal/Stoker 3 26A 120 90.63 <0.38<0.050<5.41E-04
WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack Solid/Biomass/Dutch oven 1 26 60 4.27 45.811.3006.40E-02 47.2 WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack Solid/Biomass/Dutch oven 2 26 60 4.11 34.38.4604.80E-02 35.3 WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack Solid/Biomass/Dutch oven 3 26 60 4.07 15.93.910 2.20E-02 16.2 WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct Solid/Biomass/Dutch oven 1 26 60 3.73 1.610.049 3.00E-04 1.21 WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct Solid/Biomass/Dutch oven 2 26 60 3.93 2.060.063 4.00E-04 1.55 WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct Solid/Biomass/Dutch oven 3 26 60 3.90 1.150.034 2.00E-04 0.767 WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack Solid/Biomass/Dutch oven 1 26A 120 80.65 11.13.100 3.20E-02 19.1 WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack Solid/Biomass/Dutch oven 2 26A 120 81.65 8.962.570 2.60E-02 16.4 WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack Solid/Biomass/Dutch oven 3 26A 120 83.66 6.1 1.700 1.80E-02 11.9 WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct Solid/Biomass/Dutch oven 1 26A 120 80.70 0.5370.023 2.00E-04 0.957 WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct Solid/Biomass/Dutch oven 2 26A 120 81.13 0.6230.027 3.00E-04 1.17 WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct Solid/Biomass/Dutch oven 3 26A 120 83.84 0.4280.0192.00E+00 0.875
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 1 26A 0.350
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 2 26A 0.390
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 3 26A 0.410
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 1 26A 0.200

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit Category/Subcategory**  **Run # Method used**  **(26 or 26A) Sample time** 

**(min.) Sample volume** 

**(dscf) Percent H2O** 

**(Bws) Mass Cl2** 

**(ug) Mass HF** 

**(ug) Mass HCL** 

**(ug) ppm** **lb/hr lb/MMBtu** **ppm @ 7% O2**  **Reported Mass/Unit**

WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 2 26A 0.240
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 3 26A 0.170 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 1 26A 60 43.87 58.2805.36E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 2 26A 60 43.97 32.4902.98E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 3 26A 60 44.02 78.4607.73E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 1 26A 60 4.52 2.090 5.60E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 2 26A 60 46.49 1.8404.50E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 3 26A 60 47.52 2.240 5.60E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 4 26A 60 51.49 35.0903.23E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 5 26A 60 51.95 38.3703.50E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 6 26A 60 54.23 32.3702.74E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 1 26A 60 37.95 1.260 3.60E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 2 26A 60 38.60 2.020 5.80E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 3 26A 60 38.07 2.020 5.90E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 1 26A 60 44.97 27.6802.94E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 2 26A 60 42.41 30.1303.84E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 Solid/Coal/FB 3 26A 60 43.44 27.1303.39E-02 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 1 26A 60 47.93 1.190 3.00E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 2 26A 60 50.50 1.9404.50E-03 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 Solid/Coal/FB 3 26A 60 50.03 2.0604.80E-03
WINewPageBiron/B24 Solid/Coal/Stoker 1 26A 60 59.19 5290 0.370.272 5.40E-04 WINewPageBiron/B24 Solid/Coal/Stoker 2 26A 60 39.32 5720 0.360.253 5.20E-04 WINewPageBiron/B24 Solid/Coal/Stoker 3 26A 60 36.66 5040 0.480.331 7.00E-04 WINewPage-WisconsinRapids/Power Boiler 1 - B21 Solid/Coal/Stoker 1 26A 60 43.51 0.190.116 2.70E-04 WINewPage-WisconsinRapids/Power Boiler 1 - B21 Solid/Coal/Stoker 2 26A 60 39.61 0.960.531 1.37E-03 WINewPage-WisconsinRapids/Power Boiler 1 - B21 Solid/Coal/Stoker 3 26A 60 41.54 0.5 0.297 7.10E-04 WINewPage-WisconsinRapids/Power Boiler 2 - B20 Solid/Coal/Stoker 1 26A 60 0.342 1.00E-03 WINewPage-WisconsinRapids/Power Boiler 2 - B20 Solid/Coal/Stoker 2 26A 60 0.457 1.20E-03 WINewPage-WisconsinRapids/Power Boiler 2 - B20 Solid/Coal/Stoker 3 26A 60 0.3088.00E-04 WINewPage-WisconsinRapids/Power Boiler 2 - B20 Solid/Coal/Stoker 3 26A 60 4.090 1.00E-02 WINewPage-WisconsinRapids/Power Boiler 2 - B20 Solid/Coal/Stoker 4 26A 60 <0.050<0.0001 ARPotlatchForestWarren/wellons Boiler Solid/Biomass/Stoker 1 26A 60 0.2408.00E-04 ARPotlatchForestWarren/wellons Boiler Solid/Biomass/Stoker 2 26A 60 0.630 2.10E-03 ARPotlatchForestWarren/wellons Boiler Solid/Biomass/Stoker 3 26A 60 0.540 1.80E-03 ARPotlatchForestWarren/wellons Boiler Solid/Biomass/Stoker 1 26A 60 <0.00344<0.00117<3.61E-06 ARPotlatchForestWarren/wellons Boiler Solid/Biomass/Stoker 2 26A 60 <0.00349<0.00123<3.69E-06 ARPotlatchForestWarren/wellons Boiler Solid/Biomass/Stoker 3 26A 60 <0.00356<0.00124<3.78E-06 AZCatalystPaperSnowflake/Power Boiler # 2 Solid/Coal/PC 1 26A 60 0.195 AZCatalystPaperSnowflake/Power Boiler # 2 Solid/Coal/PC 2 26A 60 0.082 AZCatalystPaperSnowflake/Power Boiler # 2 Solid/Coal/PC 3 26A 60 0.095 IAArchersDanielsMidlandDesMoines/Asea Boiler #1 Solid/Coal/FB 1 FTIR 240 <0.3<0.0661<0.000381 IAArchersDanielsMidlandDesMoines/Asea Boiler #1 Solid/Coal/FB 2 FTIR 240 <0.3<0.0654<0.000377 IAArchersDanielsMidlandDesMoines/Asea Boiler #1 Solid/Coal/FB 3 FTIR 240 <0.3<0.0694<0.000407 IDPotlatch/PB -1 CE Solid/Biomass/Fuel Cell 1 26 60 <0.012<0.00084<2.82E-05 IDPotlatch/PB -1 CE Solid/Biomass/Fuel Cell 2 26 60 <0.012<0.00084<2.84E-05 IDPotlatch/PB -1 CE Solid/Biomass/Fuel Cell 3 26 60 <0.012<0.00085<2.85E-05 IDTASCOPaul/Erie city boiler Solid/Coal/FB 1 26A 64 38.30 <0.025<0.0082 IDTASCOPaul/Erie city boiler Solid/Coal/FB 2 26A 64 43.50 <0.023<0.0088 IDTASCOPaul/Erie city boiler Solid/Coal/FB 3 26A 64 43.30 <0.022<0.0082 MSWeyerhaeuserBruce/AA-002 no. 2 Solid/Biomass/Fuel Cell 1 26A 120 95.87 0.340.0514.70E-04 MSWeyerhaeuserBruce/AA-002 no. 2 Solid/Biomass/Fuel Cell 2 26A 120 88.88 0.480.067 6.60E-04 MSWeyerhaeuserBruce/AA-002 no. 2 Solid/Biomass/Fuel Cell 3 26A 120 98.58 0.270.035 3.90E-04 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 1 26A 60 36.33 0.257 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 2 26A 60 36.16 <0.096 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 3 26A 60 37.29 <0.097 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 1 26A 60 41.58 1.695 1.20E-03 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 2 26A 60 37.00 1.817 1.30E-03 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 3 26A 60 36.63 1.953 1.50E-03 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 1 26A 60 52.81 0.123 8.95E-05 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 2 26A 60 53.52 <0.0824<0.0000601 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 3 26A 60 52.95 <0.0699<0.0000510 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 1 26A 240 159.27 3.077 2.35E-03 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 2 26A 240 160.13 2.688 2.13E-03 SCCogenSouth/B001 - Main Boiler Solid/Biomass/Stoker 3 26A 240 162.55 2.953 2.15E-03 SCMilliken-Dewey/D30 Liquid 1 26A 120 84.03 <0.0003<0.0001 SCMilliken-Dewey/D30 Liquid 2 26A 120 87.80 <0.0003<0.0001 SCMilliken-Dewey/D30 Liquid 3 26A 120 84.71 <0.0003<0.0001 TNInvistaChattanooga/EU003 - Vaporizer #2 Liquid 1 26A 60 40.63 <0.46<0.01<6.18E-04 TNInvistaChattanooga/EU003 - Vaporizer #2 Liquid 2 26A 60 37.14 <0.49<0.01<6.19E-04

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit Category/Subcategory**  **Run # Method used**  **(26 or 26A) Sample time** 

**(min.) Sample volume** 

**(dscf) Percent H2O** 

**(Bws) Mass Cl2** 

**(ug) Mass HF** 

**(ug) Mass HCL** 

**(ug) ppm** **lb/hr lb/MMBtu** **ppm @ 7% O2**  **Reported Mass/Unit**

TNInvistaChattanooga/EU003 - Vaporizer #2 Liquid 3 26A 60 37.67 <0.48<0.01<6.24E-04 TNMilanArmyAmmunitionPlant Liquid 1 26A 120 <0.05 <0.000058 TNMilanArmyAmmunitionPlant Liquid 2 26A 120 <0.05 <0.000059 TNMilanArmyAmmunitionPlant Liquid 3 26A 120 <0.05 <0.000062

TXDibollTemple-Inland/PB-44 Solid/Biomass/Dutch oven 1 26A 60 33.87 <0.0104<0.0006

TXDibollTemple-Inland/PB-44 Solid/Biomass/Dutch oven 2 26A 60 34.49 <0.0101<0.0006

TXDibollTemple-Inland/PB-44 Solid/Biomass/Dutch oven 3 26A 60 34.04 <0.0099<0.0006 WAWeyerhaeuser_Raymond/Hog Fuel Boiler EU1 Solid/Biomass/Fuel Cell 1 26 240 <607<0.129<0.017<2.7E-04 WAWeyerhaeuser_Raymond/Hog Fuel Boiler EU1 Solid/Biomass/Fuel Cell 2 26 240 <658<0.140<0.017<2.8E-04 WAWeyerhaeuser_Raymond/Hog Fuel Boiler EU1 Solid/Biomass/Fuel Cell 3 26 240 <658<0.140<0.017<2.5E-04
WINewPageBiron/B24 Solid/Coal/Stoker 1 26A 120 86.29 1.4270.894 2.00E-03
WINewPageBiron/B24 Solid/Coal/Stoker 2 26A 120 95.46 1.3950.963 1.95E-03
WINewPageBiron/B24 Solid/Coal/Stoker 3 26A 120 93.09 1.260.885 2.17E-03 WVMountainStateCarbonFollansbee/S1 Process Gas 1 26A 120 87.03 3800 1.010.081 1.40E-03 WVMountainStateCarbonFollansbee/S1 Process Gas 2 26A 120 86.64 3300 0.890.070 1.20E-03 WVMountainStateCarbonFollansbee/S1 Process Gas 3 26A 120 81.97 3100 0.880.068 1.10E-03

FLUSSugarCorp/Boiler No. 4 Solid/Biomass/Suspension/Grate 2 26.A 60 37.50 2160 1.157

FLUSSugarCorp/Boiler No. 4 Solid/Biomass/Suspension/Grate 3 26.A 60 36.83 2060 1.818

FLUSSugarCorp/Boiler No. 4 Solid/Biomass/Suspension/Grate 4 26.A 60 36.03 1540 1.892
FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 1 26.A 60 54.14 2.06 0.933 1.80E-03
FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 2 26.A 60 50.79 1.65 0.748 1.40E-03
FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 3 26.A 60 50.96 6.17 2.8145.70E-03

FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 2 26.A 60 38.28 28.7 15.6933.13E-02

FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 3 26.A 60 38.90 44.1 23.7045.31E-02

FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 4 26.A 50 32.90 30.7 19.6254.26E-02

FLUSSugarCorp/Boiler No. 7 Solid/Biomass/Suspension/Grate 5 26.A 60 37.77 20.5 11.2602.64E-02 GAGPMadisonPly/800WoodWaste Boiler Solid/Biomass/Stoker 1 26 240 17.89 46 0.060.0169.00E-05 0.07 GAGPMadisonPly/800WoodWaste Boiler Solid/Biomass/Stoker 2 26 240 17.62 64 0.080.021 1.20E-04 0.09 GAGPMadisonPly/800WoodWaste Boiler Solid/Biomass/Stoker 3 26 240 16.36 <20 <0.03<0.0072<0.00004 <0.03

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit** AKDoyonUtilities_AK/4 AKDoyonUtilities_AK/4 AKDoyonUtilities_AK/4 AKDoyonUtilities_AK/7 AKDoyonUtilities_AK/7 AKDoyonUtilities_AK/7 IAMuscatinePowerandWater/7 IAMuscatinePowerandWater/7 IAMuscatinePowerandWater/7

IDAmalgamatedSugarCoTwinFalls IDAmalgamatedSugarCoTwinFalls IDAmalgamatedSugarCoTwinFalls IDTASCOPaul/B&W Boiler IDTASCOPaul/B&W Boiler IDTASCOPaul/B&W Boiler ILPrairiePowerPearl/B1 ILPrairiePowerPearl/B1 ILPrairiePowerPearl/B1 INSABICInnovativePlastics/09-002 06-27-06 INSABICInnovativePlastics/09-002 06-27-06 INSABICInnovativePlastics/09-002 06-27-06 INSABICInnovativePlastics/09-002 04-6-2005 INSABICInnovativePlastics/09-002 04-6-2005 INSABICInnovativePlastics/09-002 04-6-2005 LAGPPortHudson/no.6 LAGPPortHudson/no.6 LAGPPortHudson/no.6
MICityofEscanaba/EUBoiler no. 1
MICityofEscanaba/EUBoiler no. 1
MICityofEscanaba/EUBoiler no. 1 MNAmericanCrystalMoorhead/Boiler 3 MNAmericanCrystalMoorhead/Boiler 3 MNAmericanCrystalMoorhead/Boiler 3 ALBoiseWhitePaperJackson ALBoiseWhitePaperJackson ALBoiseWhitePaperJackson ALIPCourtlandNo. 3 Comb Blr ALIPCourtlandNo. 3 Comb Blr ALIPCourtlandNo. 3 Comb Blr ARAnthonyForestProducts/SN-12 ARAnthonyForestProducts/SN-12 ARAnthonyForestProducts/SN-12
IARoquetteAmerica/Circulating Fluidized Bed Boiler (121)
IARoquetteAmerica/Circulating Fluidized Bed Boiler (121)
IARoquetteAmerica/Circulating Fluidized Bed Boiler (121) MEBoralexStratton/Boiler #1 MEBoralexStratton/Boiler #1 MEBoralexStratton/Boiler #1 MSHoodWaynesboro/AA-001 (wood-fired boiler) MSHoodWaynesboro/AA-001 (wood-fired boiler) MSHoodWaynesboro/AA-001 (wood-fired boiler) NCGPRoxboro/ES-1 NCGPRoxboro/ES-1 NCGPRoxboro/ES-1 NDCargillWestFargo/Foster Wheeler Boiler (EU43) NDCargillWestFargo/Foster Wheeler Boiler (EU43) NDCargillWestFargo/Foster Wheeler Boiler (EU43) NDMinnDakFarmers/Babcock and Wilcox Boiler #5 NDMinnDakFarmers/Babcock and Wilcox Boiler #5 NDMinnDakFarmers/Babcock and Wilcox Boiler #5 ORRoseburgCoquille/Boiler 1 ORRoseburgCoquille/Boiler 1 ORRoseburgCoquille/Boiler 1 ORRoseburgCoquille/Boiler 1 ORRoseburgCoquille/Boiler 1 ORRoseburgCoquille/Boiler 1 

### Analyzed in 28 **days? y/n Post-test purge?** 

**y/n Reported** 

**detection limit Meter cal** 

**y/n Leak check** 

**y/n Iso Check** 

**y/n Nozzle check** 

**y/n Notes:** 

y 100ug y y Report contains some data from lab. Saw no obvious issues. y 100ug y y Report contains some data from lab. Saw no obvious issues. y 100ug y y Report contains some data from lab. Saw no obvious issues.
y 100ug y y Report contains some data from lab. Saw no obvious issues. y 100ug y y Report contains some data from lab. Saw no obvious issues. y 100ug y y Report contains some data from lab. Saw no obvious issues.
y none given y y y Report only contained summary sheet of lab results y none given y y y Report only contained summary sheet of lab results y none given y y y Report only contained summary sheet of lab results

y 5ug CL Field data sheet for M26 -run1 was changed and run time lengthened to 62.5 minutes. Not much data from lab. y 5ug CL Not much data from lab. y 5ug CL Not much data from lab.
y .04 mg Report says results below MRL (Method Reporting Limit). y .042 mg Report says results below MRL (Method Reporting Limit). y .039 mg Report says results below MRL (Method Reporting Limit).
y 0.03mg Only 1 page summary of lab results. y 0.03mg Run 2 Field data sheet not included. y 0.03mg Only 1 page summary of lab results.
y y 6-27-2006 test date. Report calls 09-002 - Boiler House 1. No HCL lab data given for Boiler house 1 tests. y y 6-27-2006 test date. Report calls 09-002 - Boiler House 1. No HCL lab data given for Boiler house 1 tests. y y 6-27-2006 test date. Report calls 09-002 - Boiler House 1. No HCL lab data given for Boiler house 1 tests.
y y Report calls 09-002 - Boiler House 1. No lab data included for M26. 4-6-2005 test date y y Report calls 09-002 - Boiler House 1. No lab data included for M26. 4-6-2005 test date y y Report calls 09-002 - Boiler House 1. No lab data included for M26. 4-6-2005 test date
y y Very little lab data other than results y y Very little lab data other than results y y Very little lab data other than results

y 50ug y y Very little lab data other than results - only 1 page with HCl results. It appears they subtracted the DL of 50 mg from the results supplied by the lab, before they calculated the emissions rate.

y 50ug y y Very little lab data other than results - only 1 page with HCl results. It appears they subtracted the DL of 50 mg from the results supplied by the lab, before they calculated the emissions rate.

y 50ug y y Very little lab data other than results - only 1 page with HCl results. It appears they subtracted the DL of 50 mg from the results supplied by the lab, before they calculated the emissions rate.
y 2ug HCL/Sample y Very little lab data other than results y 2ug HCL/Sample y Very little lab data other than results y 2ug HCL/Sample y Very little lab data other than results
y y y y y Very little lab data other than results y y y y y Very little lab data other than results y y y y y Very little lab data other than results
y y y y y Very little lab data other than results y y y y y Very little lab data other than results y y y y y Very little lab data other than results
y y y y Substantial amount of lab data presented. y y y y Substantial amount of lab data presented. y y y y Substantial amount of lab data presented.

y y y y Substantial amount of lab data presented.

y y y y Substantial amount of lab data presented.

y y y y Substantial amount of lab data presented.
y Supporting documents can be found in file titled "Appendix.pdf" y Supporting documents can be found in file titled "Appendix.pdf" y Supporting documents can be found in file titled "Appendix.pdf"

No field or lab data included. Runs 2&3 twice as long as Run 1. No field or lab data included. Runs 2&3 twice as long as Run 1. No field or lab data included. Runs 2&3 twice as long as Run 1.
y 205ug y y y y y 226ug y y y y y 218ug y y y y 100ug y 100ug y 100ug y y y For this run fuel was "No Barge Wood". y y For this run fuel was "No Barge Wood". y y For this run fuel was "50% Barge Wood". y y For this run fuel was "50% Barge Wood". y y For this run fuel was "100% Barge Wood". y y For this run fuel was "100% Barge Wood".

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit** ORRoseburgRiddle2/Boiler 2 ORRoseburgRiddle2/Boiler 2 ORRoseburgRiddle2/Boiler 2

PADomtarJohnsonburg/#81 Coal Boiler

PADomtarJohnsonburg/#81 Coal Boiler

PADomtarJohnsonburg/#81 Coal Boiler

PADomtarJohnsonburg/#81 Coal Boiler

PADomtarJohnsonburg/#81 Coal Boiler

PADomtarJohnsonburg/#81 Coal Boiler SCMarlboroPaper/hogged Fuel Boiler SCMarlboroPaper/hogged Fuel Boiler SCMarlboroPaper/hogged Fuel Boiler TNBowaterNewsprint/Bubbling FB Boiler TNBowaterNewsprint/Bubbling FB Boiler TNBowaterNewsprint/Bubbling FB Boiler TNDomtar2384/HFB1-1 TNDomtar2384/HFB1-1 TNDomtar2384/HFB1-1 TNEastman_NO_CBIDATA/Boiler 30 TNEastman_NO_CBIDATA/Boiler 30 TNEastman_NO_CBIDATA/Boiler 30 TNInvistaChattanoogaEU003 - Vaporizer 2 TNInvistaChattanoogaEU003 - Vaporizer 2 TNInvistaChattanoogaEU003 - Vaporizer 2 VASmurfitStoneWestpt/PB08 VASmurfitStoneWestpt/PB08 VASmurfitStoneWestpt/PB08 VASmurfitStoneWestpt/PB08 VASmurfitStoneWestpt/PB08 VAUniversityofVirginia/7103-1-01R VAUniversityofVirginia/7103-1-01R VAUniversityofVirginia/7103-1-01R
WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack WAGraysHarborPaper/No. 6 Boiler (EU2)/Stack WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct WAGraysHarborPaper/No. 6 Boiler (EU2)/Duct
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 

### Analyzed in 28 **days? y/n Post-test purge?** 

**y/n Reported** 

**detection limit Meter cal** 

**y/n Leak check** 

**y/n Iso Check** 

**y/n Nozzle check** 

**y/n Notes:** 

y y y

y y According to test report Units 81 & 82 share a common stack and according to the process data both units 81&82 ran during all test runs. Therefore, data reported is for both units, not just Unit 81. Also, according to report Runs 1-3 are for test conditon A and runs 4-6 are for test condition B, but I could not find these conditions defined within report.

y y According to test report Units 81 & 82 share a common stack and according to the process data both units 81&82 ran during all test runs. Therefore, data reported is for both units, not just Unit 81. Also, according to report Runs 1-3 are for test conditon A and runs 4-6 are for test condition B, but I could not find these conditions defined within report.

y y According to test report Units 81 & 82 share a common stack and according to the process data both units 81&82 ran during all test runs. Therefore, data reported is for both units, not just Unit 81. Also, according to report Runs 1-3 are for test conditon A and runs 4-6 are for test condition B, but I could not find these conditions defined within report.

y y According to test report Units 81 & 82 share a common stack and according to the process data both units 81&82 ran during all test runs. Therefore, data reported is for both units, not just Unit 81. Also, according to report Runs 1-3 are for test conditon A and runs 4-6 are for test condition B, but I could not find these conditions defined within report.

y y According to test report Units 81 & 82 share a common stack and according to the process data both units 81&82 ran during all test runs. Therefore, data reported is for both units, not just Unit 81. Also, according to report Runs 1-3 are for test conditon A and runs 4-6 are for test condition B, but I could not find these conditions defined within report.

y y According to test report Units 81 & 82 share a common stack and according to the process data both units 81&82 ran during all test runs. Therefore, data reported is for both units, not just Unit 81. Also, according to report Runs 1-3 are for test conditon A and runs 4-6 are for test condition B, but I could not find these conditions defined within report.
y y y y y y y y y y y y y y y y y y y y y y y y Test Report says "No.8 Power Boiler with Oil" for these runs. Test Report says "No.8 Power Boiler with Oil" for these runs.

y y y

Data for Boiler 9, stack 10 - no HCL raw data found in Attachment 13 of test report only a summary of results Test Dates October 27-29, 1992 Data for Boiler 9, stack 10 - no HCL raw data found in Attachment 13 of test report only a summary of results Test Dates October 27-29, 1992 Data for Boiler 9, stack 10 - no HCL raw data found in Attachment 13 of test report only a summary of results Test Dates October 27-29, 1992 Data for Boiler 9, stack 11 - no HCL raw data found in Attachment 13 of test report only a summary of results. Test Dates October 27-29, 1992. Data for stack and duct components must be combined before use in any analysis. This correction was made in the MACT floor analysis.

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit**

WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11
WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 10 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11 WIGPGreenBay2818/B29 - FB Boiler no. 9/Stack 11
WINewPageBiron/B24 WINewPageBiron/B24 WINewPageBiron/B24 WINewPage-WisconsinRapids/Power Boiler 1 - B21 WINewPage-WisconsinRapids/Power Boiler 1 - B21 WINewPage-WisconsinRapids/Power Boiler 1 - B21 WINewPage-WisconsinRapids/Power Boiler 2 - B20 WINewPage-WisconsinRapids/Power Boiler 2 - B20 WINewPage-WisconsinRapids/Power Boiler 2 - B20 WINewPage-WisconsinRapids/Power Boiler 2 - B20 WINewPage-WisconsinRapids/Power Boiler 2 - B20 ARPotlatchForestWarren/wellons Boiler ARPotlatchForestWarren/wellons Boiler ARPotlatchForestWarren/wellons Boiler ARPotlatchForestWarren/wellons Boiler ARPotlatchForestWarren/wellons Boiler ARPotlatchForestWarren/wellons Boiler AZCatalystPaperSnowflake/Power Boiler # 2 AZCatalystPaperSnowflake/Power Boiler # 2 AZCatalystPaperSnowflake/Power Boiler # 2 IAArchersDanielsMidlandDesMoines/Asea Boiler #1 IAArchersDanielsMidlandDesMoines/Asea Boiler #1 IAArchersDanielsMidlandDesMoines/Asea Boiler #1 IDPotlatch/PB -1 CE IDPotlatch/PB -1 CE IDPotlatch/PB -1 CE IDTASCOPaul/Erie city boiler IDTASCOPaul/Erie city boiler IDTASCOPaul/Erie city boiler MSWeyerhaeuserBruce/AA-002 no. 2 MSWeyerhaeuserBruce/AA-002 no. 2 MSWeyerhaeuserBruce/AA-002 no. 2 SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCCogenSouth/B001 - Main Boiler SCMilliken-Dewey/D30 SCMilliken-Dewey/D30 SCMilliken-Dewey/D30 TNInvistaChattanooga/EU003 - Vaporizer #2 TNInvistaChattanooga/EU003 - Vaporizer #2 

### Analyzed in 28 **days? y/n Post-test purge?** 

**y/n Reported** 

**detection limit Meter cal** 

**y/n Leak check** 

**y/n Iso Check** 

**y/n Nozzle check** 

**y/n Notes:** 

Data for Boiler 9, stack 11 - no HCL raw data found in Attachment 13 of test report only a summary of results. Test Dates October 27-29, 1992. Data for Boiler 9, stack 11 - no HCL raw data found in Attachment 13 of test report only a summary of results. Test Dates October 27-29, 1992. Data for Boiler 9, stack 10, Testing performed in July, 2005 Data for Boiler 9, stack 10, Testing performed in July, 2005 Data for Boiler 9, stack 10, Testing performed in July, 2005 Data for Boiler 9, stack 11, Testing performed in July, 2005 Data for Boiler 9, stack 11, Testing performed in July, 2005 Data for Boiler 9, stack 11, Testing performed in July, 2005 Data for Boiler 9, stack 10, Testing performed in August 2004 Data for Boiler 9, stack 10, Testing performed in August 2004 Data for Boiler 9, stack 10, Testing performed in August 2004 Data for Boiler 9, stack 11, Testing performed in August 2004 Data for Boiler 9, stack 11, Testing performed in August 2004 Data for Boiler 9, stack 11, Testing performed in August 2004 Data for Boiler 9, stack 10, Testing performed in August 2006 Data for Boiler 9, stack 10, Testing performed in August 2006 Data for Boiler 9, stack 10, Testing performed in August 2006 Data for Boiler 9, stack 11, Testing performed in August 2006 Data for Boiler 9, stack 11, Testing performed in August 2006 Data for Boiler 9, stack 11, Testing performed in August 2006 Volume sampled for this run is about 50% higher for this run than for Runs 2&3, while the stack flow rate was realatively constant for all three runs. Only recorded data form 9-12-2007 testing Only recorded data form 9-12-2007 testing Only recorded data form 9-12-2007 testing

Results for Test 3 performed on May 21, 2003 Results for Test 3 performed on May 21, 2003 Results for Test 3 performed on May 21, 2003 Page 7 of report say that Runs 1 & 2 of Test 4 were not included due to issues with the boiler fuel mix. Page 7 of report say that Runs 1 & 2 of Test 4 were not included due to issues with the boiler fuel mix.

According to lab data, Runs 2 & 3 were below the MDL According to lab data, Runs 2 & 3 were below the MDL

According to lab data, Runs 2 & 3 were below the MDL According to lab data, Runs 2 & 3 were below the MDL No data from lab included in report. No data from lab included in report. No data from lab included in report.

## Appendix D - HCl Tracking Sheet for Boiler Data Review **Facility/Unit** TNInvistaChattanooga/EU003 - Vaporizer #2 TNMilanArmyAmmunitionPlant TNMilanArmyAmmunitionPlant TNMilanArmyAmmunitionPlant

TXDibollTemple-Inland/PB-44

TXDibollTemple-Inland/PB-44

TXDibollTemple-Inland/PB-44 WAWeyerhaeuser_Raymond/Hog Fuel Boiler EU1 WAWeyerhaeuser_Raymond/Hog Fuel Boiler EU1 WAWeyerhaeuser_Raymond/Hog Fuel Boiler EU1
WINewPageBiron/B24
WINewPageBiron/B24
WINewPageBiron/B24 WVMountainStateCarbonFollansbee/S1 WVMountainStateCarbonFollansbee/S1 WVMountainStateCarbonFollansbee/S1

FLUSSugarCorp/Boiler No. 4

FLUSSugarCorp/Boiler No. 4

FLUSSugarCorp/Boiler No. 4
FLUSSugarCorp/Boiler No. 7
FLUSSugarCorp/Boiler No. 7
FLUSSugarCorp/Boiler No. 7

FLUSSugarCorp/Boiler No. 7

FLUSSugarCorp/Boiler No. 7

FLUSSugarCorp/Boiler No. 7

FLUSSugarCorp/Boiler No. 7 GAGPMadisonPly/800WoodWaste Boiler GAGPMadisonPly/800WoodWaste Boiler GAGPMadisonPly/800WoodWaste Boiler 

### Analyzed in 28 **days? y/n Post-test purge?** 

**y/n Reported** 

**detection limit Meter cal** 

**y/n Leak check** 

**y/n Iso Check** 

**y/n Nozzle check** 

**y/n Notes:** 

Report says they did a modified version of Method 26, which appears to mean single point sampling with a 26A sampling train - big impingers. Then used data from simultaneous Method 5 train to calculate lb/hr numbers. Doesn't necessarily invalidate the data - just odd. All HCL values were below the detection limit. Report says they did a modified version of Method 26, which appears to mean single point sampling with a 26A sampling train - big impingers. Then used data from simultaneous Method 5 train to calculate lb/hr numbers. Doesn't necessarily invalidate the data - just odd. All HCL values were below the detection limit. Report says they did a modified version of Method 26, which appears to mean single point sampling with a 26A sampling train - big impingers. Then used data from simultaneous Method 5 train to calculate lb/hr numbers. Doesn't necessarily invalidate the data - just odd. All HCL values were below the detection limit. No lab or field data included. Only a summary of results. No lab or field data included. Only a summary of results. No lab or field data included. Only a summary of results. According to page 19 of test report - bark was also being combusted during test program. Only a summary of the lab data was provided. According to page 19 of test report - bark was also being combusted during test program. Only a summary of the lab data was provided. According to page 19 of test report - bark was also being combusted during test program. Only a summary of the lab data was provided.

Bagasse and oil used to fire boiler according to report. Found several mistakes in the data, beginning with the fact that the flow rates were the same for all three run. Recalculated flows and lb/hr numbers. Recalculated values are highlighted in red. Due to time constraints and unique F-factor treatment for bagasse boilers, this change was not made in the database, but it will be investigated before promulgation of the final rule.
Bagasse and oil used to fire boiler according to report. Found several mistakes in the data, beginning with the fact that the flow rates were the same for all three run. Recalculated flows and lb/hr numbers. Recalculated values are highlighted in red. Due to time constraints and unique F-factor treatment for bagasse boilers, this change was not made in the database, but it will be investigated before promulgation of the final rule. Bagasse and oil used to fire boiler according to report. Found several mistakes in the data, beginning with the fact that the flow rates were the same for all three run. Recalculated flows and lb/hr numbers. Recalculated values are highlighted in red. Due to time constraints and unique F-factor treatment for bagasse boilers, this change was not made in the database, but it will be investigated before promulgation of the final rule. Please note that the emissions numbers for Run 3 are 3+ times larger that Runs 1 &2. Report says boiler was fired on Bagasse only. Please note that the emissions numbers for Run 3 are 3+ times larger that Runs 1 &2. Report says boiler was fired on Bagasse only. Please note that the emissions numbers for Run 3 are 3+ times larger that Runs 1 &2. Report says boiler was fired on Bagasse only.

According to report Run 1 was no included due to flow measurement issues and Run4 only lasted 50 minutes because of clogged feeder lines. According to report, boiler was fired with a nominal 50/50 blend of wood chips and bagasse.
According to report Run 1 was no included due to flow measurement issues and Run4 only lasted 50 minutes because of clogged feeder lines. According to report, boiler was fired with a nominal 50/50 blend of wood chips and bagasse.
According to report Run 1 was no included due to flow measurement issues and Run4 only lasted 50 minutes because of clogged feeder lines. According to report, boiler was fired with a nominal 50/50 blend of wood chips and bagasse.
According to report Run 1 was no included due to flow measurement issues and Run4 only lasted 50 minutes because of clogged feeder lines. According to report, boiler was fired with a nominal 50/50 blend of wood chips and bagasse. Summary sheet in test report gives HCL results as mg, should be ug. Results appear to be correct. Summary sheet in test report gives HCL results as mg, should be ug. Results appear to be correct. Summary sheet in test report gives HCL results as mg, should be ug. Results appear to be correct.