g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

1

EQUIPMENT SUMMARY & LEADTIME LISTING 

In accordance with our interpretation of the plans and specifications, and subject to approval, 

GE Industrial C&I, is pleased to offer the following bill of material for your consideration. This 

offer is conditional upon your acceptance of the applicable, GE C&I Industrial Systems Selling 

Policy FN-1090 and Pricing Policy 1Q. Schedules are based on current factory scheduling. 

Contact GE Distributor or GE Industrial C&I if different dates are required. Dates are based on 

receipt of an order with complete information at manufacturing location. Approval drawings 

must be returned marked "FOR MANUFACTURE". 

QTY EQUIPMENT 

WEEKS FOR 

APPROVAL 

DRAWINGS 

SUBMITTAL 

SHIPMENT 

WEEKS 

AFTER 

DRAWING 

RELEASE 

4 8000 SERIES MOTOR CONTROL 

CENTERS 

4-5 14-16 

 

Drawing review and return time for all equipment is 30 Days maximum. 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

2

Base Bill of Material 

- 

Item# Qty Description 

 1 1 8000 Series MCC (GO100) 

MCC 1C31 

 8000 Line, UL labeling required, NEMA Wiring Class, I-BD, NEMA Enclosure NEMA 

 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 

 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied 

 Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps 

Enclosure and Bus (18 Vertical Sections) 

 17 NEMA Enclosure : 1G, 20" wide 

 1 NEMA Enclosure : 1G, 30" wide 

 Enclosure Modifications 

 (18) Steel bottom plates 

 (18) Space Heaters (less controls) 

 (1) Thermostatic Control For Space Heaters 

 (1) Circuit Breaker for Space Heater Circuit 

 Bus System 

 (18) 800 Amp CU Main Bus 

 (18) 300 Amp CU Ground Bus 

 (15) 300 Amp CU Front Vertical Bus 

 (18) Unit Ground Bus 

 (1) 450 Amp CU Front Vertical Bus 

 (2) 600 Amp CU Front Vertical Bus 

 Bus Modifications 

 (18) Silver Plating on Main Bus 

 (18) 65000 AIC SC Bus Bracing 

 (18) Double Bolted Construction for 2" Main Bus 

 (18) Silver Plating on Vertical Bus 

 (2) Grnd Lug 

Incoming Power 

 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, 

 BOTTOM Feed CU BURNDY Lug 

 Miscellaneous 

 (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM 

Feeders 

 30 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B 

 2 SFLT Type 250 Amps Frame 225 Amps Trip Feeder C/B 

Combination Starter Devices 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

3

 (1) Solid state OL relay 

 (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 3 Size 2 FVNR Starter 25 Hp 60 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 (1) Coil Surge Suppressor 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 1 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 4 Size 3 FVR Starter 50 Hp 125 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 2 Size 3 FVNR Starter 50 Hp 125 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

4

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) CPT-300 VA 

 (1) Coil Surge Suppressor 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) C2000 AUX Control 4-pole control relay 

Lighting Panel Boards 

 1 42 Ckts AQ Panelboard with 175A MAIN CB [Branch CB (15) 15A 

 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] 

Lighting and Power Transformers 

 1 45kVA 3PH 42000 AIC with C/B w/ Primary Taps 

Miscellaneous 

 3 12" Section of Future space available 

 1 6" Section of Future space available 

Units supplied with the following options 

 31 Control wire markers - Non PVC 

 31 Control wire markers - insulated ring non PVC 

 31 High density control terminal board 

 31 SIS VW1 power wire 

 31 Non-PVC power wire markers 

 31 Non-insulated ring power wire terminal 

 31 N.O. OL contact 

Nema Wiring Class Adjustment 

 1 NEMA Wiring Class : I-B 

Order Information 

 (3) Standard Instruction Books 

 (3) Certified Test Reports 

 (3) Standard Catalog Renewal Parts Books 

 (3) 11 by 17 Print Customer Prints 

 Electronic Drawings - MailTo:[later], Drawings Format: 

 DXF and PDF 

 2 1 8000 Series MCC (GO100) 

MCC 1A71 

 8000 Line, UL labeling required, NEMA Wiring Class, I-BD, NEMA Enclosure NEMA 

 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 

 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied 

 Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps 

Enclosure and Bus (20 Vertical Sections) 

 18 NEMA Enclosure : 1G, 20" wide 

 1 NEMA Enclosure : 1G, 30" wide 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

5

 Enclosure Modifications 

 (18) Steel bottom plates 

 (18) Space Heaters (less controls) 

 (1) Thermostatic Control For Space Heaters 

 Bus System 

 (18) 800 Amp CU Main Bus 

 (18) 300 Amp CU Ground Bus 

 (15) 300 Amp CU Front Vertical Bus 

 (13) Unit Ground Bus 

 (1) 450 Amp CU Front Vertical Bus 

 (4) 600 Amp CU Front Vertical Bus 

 Bus Modifications 

 (18) Silver Plating on Main Bus 

 (18) 65000 AIC SC Bus Bracing 

 (18) Double Bolted Construction for 2" Main Bus 

 (18) Silver Plating on Vertical Bus 

 Miscellaneous 

 (2) Grnd Lug 

Incoming Power 

 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, 

 BOTTOM Feed CU BURNDY Lug 

 Miscellaneous 

 (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM 

Feeders 

 35 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B 

Combination Starter Devices 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 4 Size 2 FVNR Starter 25 Hp 60 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

6

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 1 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc. 

 Accessories 

 (1) C2000 Interposing 4-pole control relay (120V) 

 (2) CB auxiliary contact 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) CPT-300 VA 

 (1) Coil Surge Suppressor 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 4 Size 3 FVR Starter 50 Hp 125 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 Interposing 4-pole control relay (120V) 

 (1) CPT-500 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 1 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc. 

 Accessories 

 (1) C2000 Interposing 4-pole control relay (120V) 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 1 Size 3 FVNR Starter 50 Hp 125 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

7

 Accessories 

 (1) CPT-300 VA 

 (1) Coil Surge Suppressor 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) C2000 AUX Control 4-pole control relay 

Lighting Panel Boards 

 1 42 Ckts AQ Panelboard with 150A MAIN CB [Branch CB (15) 15A 

 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] 

Lighting and Power Transformers 

 1 30kVA 3PH 42000 AIC with C/B w/ Primary Taps 

Miscellaneous 

 1 6" Section of Future space available 

 4 12" Section of Future space available 

Units supplied with the following options 

 31 Control wire markers - Non PVC 

 31 High density control terminal board 

 31 SIS VW1 power wire 

 31 N.O. OL contact 

Nema Wiring Class Adjustment 

 1 NEMA Wiring Class : I-B 

Order Information 

 (3) Standard Instruction Books 

 (3) Certified Test Reports 

 (3) Standard Catalog Renewal Parts Books 

 (3) 11 by 17 Print Customer Prints 

 Electronic Drawings - MailTo:[later], Drawings Format: 

 DXF and PDF 

 3 1 8000 Series MCC (GO100) 

MCC 2C31 

 8000 Line, UL labeling required, NEMA Wiring Class, I-BD, NEMA Enclosure NEMA 

 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 

 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied 

 Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps 

Enclosure and Bus (18 Vertical Sections) 

 16 NEMA Enclosure : 1G, 20" wide 

 1 NEMA Enclosure : 1G, 30" wide 

 Enclosure Modifications 

 (16) Steel bottom plates 

 (16) Space Heaters (less controls) 

 (1) Thermostatic Control For Space Heaters 

 Bus System 

 (16) 800 Amp CU Main Bus 

 (16) 300 Amp CU Ground Bus 

 (12) 300 Amp CU Front Vertical Bus 

 (3) 600 Amp CU Front Vertical Bus 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

8

 (1) 450 Amp CU Front Vertical Bus 

 Bus Modifications 

 (16) Silver Plating on Main Bus 

 (16) 65000 AIC SC Bus Bracing 

 (16) Double Bolted Construction for 2" Main Bus 

 (16) Silver Plating on Vertical Bus 

 Miscellaneous 

 (2) Grnd Lug 

Incoming Power 

 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, 

 BOTTOM Feed CU BURNDY Lug 

 Miscellaneous 

 (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM 

Feeders 

 34 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B 

Combination Starter Devices 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 

 3 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 2 Size 2 FVNR Starter 25 Hp 60 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (2) CB auxiliary contact 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 2 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

9

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (2) CB auxiliary contact 

 (1) CPT-300 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 4 Size 3 FVR Starter 50 Hp 125 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (2) CB auxiliary contact 

 (1) CPT-500 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 1 Size 3 FVNR Starter 50 Hp 125 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) C2000 AUX Control 4-pole control relay 

Lighting Panel Boards 

 1 42 Ckts AQ Panelboard with 150A MAIN CB [Branch CB (15) 15A 

 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] 

Lighting and Power Transformers 

 1 30kVA 3PH 42000 AIC with C/B w/ Primary Taps 

Miscellaneous 

 8 12" Section of Future space available 

 1 6" Section of Future space available 

Units supplied with the following options 

 30 Control wire markers - Non PVC 

 30 High density control terminal board 

 30 SIS VW1 power wire 

 30 N.O. OL contact 

 30 6PT additional terminal boards 

Nema Wiring Class Adjustment 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

10

 1 NEMA Wiring Class : I-B 

Order Information 

 (3) Standard Instruction Books 

 (3) Certified Test Reports 

 (3) Standard Catalog Renewal Parts Books 

 (3) 11 by 17 Print Customer Prints 

 Electronic Drawings - MailTo:[later], Drawings Format: 

 DXF and PDF 

 4 1 8000 Series MCC (GO100) 

MCC 2A71 

 8000 Line, UL labeling required, NEMA Wiring Class, I-BD, NEMA Enclosure NEMA 

 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 

 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied 

 Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps 

Enclosure and Bus (19 Vertical Sections) 

 15 NEMA Enclosure : 1G, 20" wide 

 1 NEMA Enclosure : 1G, 30" wide 

 Enclosure Modifications 

 (19) Steel bottom plates 

 (19) Space Heaters (less controls) 

 (1) Thermostatic Control For Space Heaters 

 Bus System 

 (16) 800 Amp CU Main Bus 

 (16) 300 Amp CU Ground Bus 

 (9) 300 Amp CU Front Vertical Bus 

 (3) 450 Amp CU Front Vertical Bus 

 (4) 600 Amp CU Front Vertical Bus 

 Bus Modifications 

 (16) Silver Plating on Main Bus 

 (16) 65000 AIC SC Bus Bracing 

 (16) Double Bolted Construction for 2" Main Bus 

 (16) Silver Plating on Vertical Bus 

 Miscellaneous 

 (2) Grnd Lug 

Incoming Power 

 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, 

 BOTTOM Feed CU BURNDY Lug 

 Miscellaneous 

 (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM 

Feeders 

 31 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B 

Combination Starter Devices 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

11

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 

 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 2 Size 2 FVNR Starter 25 Hp 50 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 1 Size 4 FVNR Starter 100 Hp 200 Amps Trip SFL C/B Disc. 

 Accessories 

 (1) C2000 Interposing 4-pole control relay (120V) 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) CPT-300 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 4 Size 3 FVR Starter 50 Hp 100 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 AUX Control 4-pole control relay 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (2) Intlks + 2(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 2 Size 3 FVNR Starter 50 Hp 100 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) C2000 Interposing 4-pole control relay (120V) 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

12

 (1) CB auxiliary contact 

 (1) Coil Surge Suppressor 

 (1) CPT-500 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) Solid state OL relay 

 Miscellaneous 

 (1) HEC#CE - Circut Breaker - 1 Pole - 120V 

 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc. 

 Accessories 

 (1) Coil Surge Suppressor 

 (1) CPT-300 VA 

 (3) Intlks + 1(No Charge)= 4 Total 

 (1) C2000 AUX Control 4-pole control relay 

Lighting Panel Boards 

 1 42 Ckts AQ Panelboard with 175A MAIN CB [Branch CB (15) 15A 

 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] 

Lighting and Power Transformers 

 1 45kVA 3PH 42000 AIC with C/B w/ Primary Taps 

Miscellaneous 

 13 12" Section of Future space available 

 13 6" Section of Future space available 

Units supplied with the following options 

 29 Control wire markers - Non PVC 

 29 High density control terminal board 

 29 SIS VW1 power wire 

 29 6PT additional terminal boards 

Nema Wiring Class Adjustment 

 1 NEMA Wiring Class : I-B 

Order Information 

 (3) Standard Instruction Books 

 (3) Certified Test Reports 

 (3) Standard Catalog Renewal Parts Books 

 (3) 11 by 17 Print Customer Prints 

 Electronic Drawings - MailTo:[later], Drawings Format: 

 DXF and PDF 

Total Lot Price $ See pricing Form*
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

13

JOB CLARIFICATION & EXCEPTIONS 

1. BID FORM – Unit pricing is firm to release for manufacture to the plants after drawing 

approval. Post release change will be at price in effect due to re-engineering and 

schedule disruption costs. 

2. Schedule of submittals – lead-times are per current schedules at time of quotation 

and subject to change, based on manufacturing plant loading. 

3. Q001.1 : – Exception - To all ISO 9000 requirements. Clarification – Testing is per 

applicable NEMA/ANSI and UL standards. Clarification - Witness of GE standard 

industry production testing is not included add $2500/MCC for the first day straight 

time. and $1000/MCC for each additional day straight-time and adds 4-5 additional 

working days to the quoted lead-times. Inspection of assemblies requires a two week 

advanced notice and is subject to GE plant restrictions on site. Exception – To any 

access to GE sub tier suppliers. 

4. Q0001.1.5.2 thru .6: Charges for materials and/or labor to remedy a problem with 

equipment will not be accepted unless prior written approval to remedy said problem 

has been obtained from GE. (see page 12 para. E). In and out charges are not 

included. 

5. Silicon Rectifier Units field mounted and connected by others. 

6. VFD units shown fed from MCC 1C31 and others are remote and by others. 
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

14

 COMMENTS, CLARIFICATIONS, SPECIAL CONDITIONS 

1. Cable terminations use mechanical type compression lugs, not (crimp) hydraulic type 

compression lugs, if crimp type lugs are applied, GE will supply provision for this type of 

lug by others. (Refer to GE distributors.) Mechanical lugs will accept either copper or 

aluminum cables (UL CU/AL rated). High voltage terminators such as potheads, stress 

cone, loadbreak and/or deadbreak elbows are not included. (Refer to GE distributors.) 

2. Floor channels, threaded bar stock, rubber mats, nameplates for any equipment, arc 

flash labeling, external isomode pads, transformer wall mountings, transformer lugs, 

externally mounted station batteries, racks and chargers are not included unless shown 

as a separate item within this bill of material. (Refer to GE distributors.) 

3. No 600V fuses (except initial limiters for Tri-Break or AKRU type circuit breakers) are 

included unless included in the description of the individual piece of equipment or listed 

as a separate item. When fuses are included in bill of material, no spares or spare fuse 

cabinets are included. (Refer to GE distributors.) 

4. Bi-metal Overload heaters for E9000 Line Motor Control Center starters only are included, 

but motor nameplate data (full load current, service factor, locked rotor kVA) must be 

forwarded prior to release for shipment. 

 

5. Unless stipulated in the aforementioned proposal, equipment proposed is finished using 

GE Products standard application process and ANSI 61 color. Equipment enclosures will 

be indoor NEMA 1 type unless shown otherwise. 

6. Coordination/Short Circuit Studies, Arc Flash Studies, field testing, taking field 

measurements, installation and/or start-up assistance by GE Engineering Service or FastTeam partners is not included unless shown as a separate item within this bill of material. 

When included, they apply to proposed new GE Products only. Refer to GE distributors 

for per diem rates. GE or GE Fast-Team Field Engineering Service will require contractor 

provided qualified electricians support.
g GE Industrial C & I, Jacksonville, Florida 

SJRPP NOx Reduction Project, Black & Veatch Corp. 

Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co. 

 

“GE Imagination at Work” 

© Copyright GE 2007

15

 TERMS & CONDITIONS SUMMARY 

 This is a partial listing. The current complete GE terms of sale with 

 A detailed explanation of terms and conditions is available from your 

 GE Distributor. 

 A. Standard Price Adjustment Clause 1Q - 

1. This quotation expires 30 calendar days from its date unless terminated sooner by notice. 

2. The prices stated herein are firm provided: 

a. The order is released, with complete engineering details, for shipment within 90 

calendar days from the date of order or at the Company’s earliest convenience 

thereafter; or 

b. If drawings for approval are required, the drawings must be returned and approved 

within 60 calendar days of the original mailing date of the drawings by the Company 

with products covered by the drawings released for manufacture. Such release must 

call for shipment within 90 calendar days from the date of order or at the Company’s 

earliest convenience thereafter. Drawing resubmittals, which are required for any 

reason other than to correct Company errors, will not extend the 60-day period for 

release. 

3. In the event that the customer for any reason does not comply with the conditions in 

paragraph 2 above and/or shipment is delayed for any reason not within control of the 

Company, the price shall be increased 1-1/2% for each full month or fraction thereof that 

shipment* is thereby delayed after the 90-day period from the date of order. 

 B. Delivery of this electrical equipment to any common carrier shall 

 constitute delivery to the purchaser; and all risk of loss and damage 

 during shipment shall pass to the purchaser at that time. 

 C. Freight charges are prepaid and included in the price F.O.B. point of 

 shipment to accessible common carrier point nearest first destination. 

 D. Standard warranty is applicable for (12) twelve months from 

 date of start-up or (18) eighteen months from shipment whichever comes first. 

 E. Charges for materials and/or labor to remedy a problem with GE 

 equipment will not be accepted unless prior written approval to remedy 

 said problem has been obtained from GE. 

 F. GE liability is limited in connection with the performance per the 

 "Force Majure" and "Limitation of Liability" limitations of GE selling policy. 

 G. Order Cancellation - Schedule of Charges:

10%-Order received and entered on factory, work not started, material not ordered. 

30%-Engineering completed &/or drawings for approval submitted. 

60%-Approved drawings returned. Job released for manufacture and shipment. 

80%-Material accumulated and production started. 

100%-Manufacturing completed.