# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 1 

### EQUIPMENT SUMMARY & LEADTIME LISTING

In accordance with our interpre tation of the plans and specific ations, and subject to approval, GE Industrial C&I, is pleased to offer the following bill of material for your consideration. This offer is conditional upon your acceptance of the applicable, GE C&I Industrial Systems Selling Policy FN-1090 and Pricing Policy 1Q. Schedules are based on current factory scheduling. Contact GE Distributor or GE Industrial C&I if different dates are required. Dates are based on receipt of an order with complete information at manufacturing location. Approval drawings must be returned mark ed "FOR MANUFACTURE".

QTY EQUIPMENT WEEKS FOR
APPROVAL
DRAWINGS
SUBMITTAL SHIPMENT
WEEKS
AFTER
DRAWING
RELEASE

4 8000 SERIES MOTOR CONTROL
CENTERS 4-5 14-16

Drawing review and return time for all equipment is 30 Days maximum.

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 2 

### Base Bill of Material

- Item# Qty Description 1 1 8000 Series MCC (GO100)

MCC 1C31 8000 Line, UL labeling required, NEMA Wiri ng Class, I-BD, NEMA Enclosure NEMA 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps Enclosure and Bus (18 Vertical Sections) 17 NEMA Enclosure : 1G, 20" wide 1 NEMA Enclosure : 1G, 30" wide Enclosure Modifications (18) Steel bottom plates (18) Space Heaters (less controls) (1) Thermostatic Control For Space Heaters (1) Circuit Breaker for Space Heater Circuit Bus System (18) 800 Amp CU Main Bus (18) 300 Amp CU Ground Bus (15) 300 Amp CU Front Vertical Bus (18) Unit Ground Bus (1) 450 Amp CU Front Vertical Bus (2) 600 Amp CU Front Vertical Bus Bus Modifications (18) Silver Plating on Main Bus (18) 65000 AIC SC Bus Bracing (18) Double Bolted Construction for 2" Main Bus (18) Silver Plating on Vertical Bus (2) Grnd Lug Incoming Power 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, BOTTOM Feed CU BURNDY Lug Miscellaneous (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM
Feeders 30 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B 2 SFLT Type 250 Amps Frame 225 Amps Trip Feeder C/B
Combination Starter Devices 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 3 (1) Solid state OL relay (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay 3 Size 2 FVNR Starter 25 Hp 60 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay (1) Coil Surge Suppressor Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 1 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay 4 Size 3 FVR Starter 50 Hp 125 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-500 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 2 Size 3 FVNR Starter 50 Hp 125 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 4 (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) CPT-300 VA (1) Coil Surge Suppressor (3) Intlks + 1(No Charge)= 4 Total (1) C2000 AUX Control 4-pole control relay Lighting Panel Boards 1 42 Ckts AQ Panelboard with 175A MAIN CB [Branch CB (15) 15A 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] Lighting and Power Transformers 1 45kVA 3PH 42000 AIC with C/B w/ Primary Taps
Miscellaneous 3 12" Section of Future space available 1 6" Section of Future space available Units supplied with the following options 31 Control wire markers - Non PVC 31 Control wire markers - insulated ring non PVC 31 High density control terminal board 31 SIS VW1 power wire 31 Non-PVC power wire markers 31 Non-insulated ring power wire terminal
31 N.O. OL contact Nema Wiring Class Adjustment 1 NEMA Wiring Class : I-B Order Information (3) Standard Instruction Books (3) Certified Test Reports (3) Standard Catalog Renewal Parts Books (3) 11 by 17 Print Customer Prints Electronic Drawings - MailT o:[later], Drawings Format: DXF and PDF

2 1 8000 Series MCC (GO100)

MCC 1A71 8000 Line, UL labeling required, NEMA Wiri ng Class, I-BD, NEMA Enclosure NEMA 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps Enclosure and Bus (20 Vertical Sections) 18 NEMA Enclosure : 1G, 20" wide 1 NEMA Enclosure : 1G, 30" wide

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 5 Enclosure Modifications (18) Steel bottom plates (18) Space Heaters (less controls) (1) Thermostatic Control For Space Heaters Bus System (18) 800 Amp CU Main Bus (18) 300 Amp CU Ground Bus (15) 300 Amp CU Front Vertical Bus (13) Unit Ground Bus (1) 450 Amp CU Front Vertical Bus (4) 600 Amp CU Front Vertical Bus Bus Modifications (18) Silver Plating on Main Bus (18) 65000 AIC SC Bus Bracing (18) Double Bolted Construction for 2" Main Bus (18) Silver Plating on Vertical Bus Miscellaneous (2) Grnd Lug Incoming Power 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, BOTTOM Feed CU BURNDY Lug Miscellaneous (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM
Feeders 35 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B
Combination Starter Devices 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay 4 Size 2 FVNR Starter 25 Hp 60 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 6 (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 1 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc.
Accessories (1) C2000 Interposing 4-pole control relay (120V) (2) CB auxiliary contact (1) Coil Surge Suppressor (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) CPT-300 VA (1) Coil Surge Suppressor (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay 4 Size 3 FVR Starter 50 Hp 125 Amps Trip SEL C/B Disc.
Accessories (1) C2000 Interposing 4-pole control relay (120V) (1) CPT-500 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 1 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc.
Accessories (1) C2000 Interposing 4-pole control relay (120V) (1) Coil Surge Suppressor (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 1 Size 3 FVNR Starter 50 Hp 125 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 7 Accessories (1) CPT-300 VA (1) Coil Surge Suppressor (3) Intlks + 1(No Charge)= 4 Total (1) C2000 AUX Control 4-pole control relay Lighting Panel Boards 1 42 Ckts AQ Panelboard with 150A MAIN CB [Branch CB (15) 15A 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] Lighting and Power Transformers 1 30kVA 3PH 42000 AIC with C/B w/ Primary Taps
Miscellaneous 1 6" Section of Future space available 4 12" Section of Future space available Units supplied with the following options 31 Control wire markers - Non PVC 31 High density control terminal board 31 SIS VW1 power wire
31 N.O. OL contact Nema Wiring Class Adjustment 1 NEMA Wiring Class : I-B Order Information (3) Standard Instruction Books (3) Certified Test Reports (3) Standard Catalog Renewal Parts Books (3) 11 by 17 Print Customer Prints Electronic Drawings - MailT o:[later], Drawings Format: DXF and PDF

3 1 8000 Series MCC (GO100)

MCC 2C31 8000 Line, UL labeling required, NEMA Wiri ng Class, I-BD, NEMA Enclosure NEMA 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps Enclosure and Bus (18 Vertical Sections) 16 NEMA Enclosure : 1G, 20" wide 1 NEMA Enclosure : 1G, 30" wide Enclosure Modifications (16) Steel bottom plates (16) Space Heaters (less controls) (1) Thermostatic Control For Space Heaters Bus System (16) 800 Amp CU Main Bus (16) 300 Amp CU Ground Bus (12) 300 Amp CU Front Vertical Bus (3) 600 Amp CU Front Vertical Bus

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 8 (1) 450 Amp CU Front Vertical Bus Bus Modifications (16) Silver Plating on Main Bus (16) 65000 AIC SC Bus Bracing (16) Double Bolted Construction for 2" Main Bus (16) Silver Plating on Vertical Bus Miscellaneous (2) Grnd Lug Incoming Power 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, BOTTOM Feed CU BURNDY Lug Miscellaneous (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM
Feeders 34 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B
Combination Starter Devices 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 3 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay 2 Size 2 FVNR Starter 25 Hp 60 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (2) CB auxiliary contact (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 2 Size 4 FVNR Starter 100 Hp 225 Amps Trip SFL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 9 Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (2) CB auxiliary contact (1) CPT-300 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay 4 Size 3 FVR Starter 50 Hp 125 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (2) CB auxiliary contact (1) CPT-500 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 1 Size 3 FVNR Starter 50 Hp 125 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) C2000 AUX Control 4-pole control relay Lighting Panel Boards 1 42 Ckts AQ Panelboard with 150A MAIN CB [Branch CB (15) 15A 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] Lighting and Power Transformers 1 30kVA 3PH 42000 AIC with C/B w/ Primary Taps
Miscellaneous 8 12" Section of Future space available 1 6" Section of Future space available Units supplied with the following options 30 Control wire markers - Non PVC 30 High density control terminal board 30 SIS VW1 power wire
30 N.O. OL contact 30 6PT additional terminal boards Nema Wiring Class Adjustment

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 10 1 NEMA Wiring Class : I-B Order Information (3) Standard Instruction Books (3) Certified Test Reports (3) Standard Catalog Renewal Parts Books (3) 11 by 17 Print Customer Prints Electronic Drawings - MailT o:[later], Drawings Format: DXF and PDF

4 1 8000 Series MCC (GO100)

MCC 2A71 8000 Line, UL labeling required, NEMA Wiri ng Class, I-BD, NEMA Enclosure NEMA 1G, 12" Top Mounted Wireway, MCC is Front Mounting Only, 480 Volts 3 Phase 3 Wire 60 Hz, Main Horz. Bus 800 Amps; Rating 65000 AIC, Per Customer supplied Specifications, Per Customer supplied drawings, Min. Vertical Bus 300 Amps Enclosure and Bus (19 Vertical Sections) 15 NEMA Enclosure : 1G, 20" wide 1 NEMA Enclosure : 1G, 30" wide Enclosure Modifications (19) Steel bottom plates (19) Space Heaters (less controls) (1) Thermostatic Control For Space Heaters Bus System (16) 800 Amp CU Main Bus (16) 300 Amp CU Ground Bus (9) 300 Amp CU Front Vertical Bus (3) 450 Amp CU Front Vertical Bus (4) 600 Amp CU Front Vertical Bus Bus Modifications (16) Silver Plating on Main Bus (16) 65000 AIC SC Bus Bracing (16) Double Bolted Construction for 2" Main Bus (16) Silver Plating on Vertical Bus Miscellaneous (2) Grnd Lug Incoming Power 1 800Amp Terminal Board With (3) 600 MCM Lugs Per Phase, BOTTOM Feed CU BURNDY Lug Miscellaneous (3) BOP#YA29/34 - Lugs - Qty. 3 250-500MCM
Feeders 31 SELT Type 100 Amps Frame 100 Amps Trip Feeder C/B
Combination Starter Devices 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 11 (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay (1) ITI#PCL20 - Transducer - Current 0-20 Amps w/CTs 2 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay 2 Size 2 FVNR Starter 25 Hp 50 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 1 Size 4 FVNR Starter 100 Hp 200 Amps Trip SFL C/B Disc.
Accessories (1) C2000 Interposing 4-pole control relay (120V) (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 4 Size 1 FVR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) CPT-300 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay 4 Size 3 FVR Starter 50 Hp 100 Amps Trip SEL C/B Disc.
Accessories (1) C2000 AUX Control 4-pole control relay (1) Coil Surge Suppressor (1) CPT-500 VA (2) Intlks + 2(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 2 Size 3 FVNR Starter 50 Hp 100 Amps Trip SEL C/B Disc.
Accessories (1) C2000 Interposing 4-pole control relay (120V)

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 12 (1) CB auxiliary contact (1) Coil Surge Suppressor (1) CPT-500 VA (3) Intlks + 1(No Charge)= 4 Total (1) Solid state OL relay Miscellaneous (1) HEC#CE - Circut Breaker - 1 Pole - 120V 12 Size 1 FVNR Starter 10 Hp 20 Amps Trip SEL C/B Disc.
Accessories (1) Coil Surge Suppressor (1) CPT-300 VA (3) Intlks + 1(No Charge)= 4 Total (1) C2000 AUX Control 4-pole control relay Lighting Panel Boards 1 42 Ckts AQ Panelboard with 175A MAIN CB [Branch CB (15) 15A 1P; (22) 20A 1P; (1) 20A 3P; (2) 30A 1P;] Lighting and Power Transformers 1 45kVA 3PH 42000 AIC with C/B w/ Primary Taps
Miscellaneous 13 12" Section of Future space available 13 6" Section of Future space available Units supplied with the following options 29 Control wire markers - Non PVC 29 High density control terminal board 29 SIS VW1 power wire 29 6PT additional terminal boards Nema Wiring Class Adjustment 1 NEMA Wiring Class : I-B Order Information (3) Standard Instruction Books (3) Certified Test Reports (3) Standard Catalog Renewal Parts Books (3) 11 by 17 Print Customer Prints Electronic Drawings - MailT o:[later], Drawings Format: DXF and PDF

Total Lot Price $ See pricing Form*

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 13 

### JOB CLARIFICATION & EXCEPTIONS

1. BID FORM – Unit pricing is firm to release for manufacture to the plants after drawing approval. Post release change will be at price in effect due to re-engineering and schedule disruption costs. 2. Schedule of submittals – lead-times are per current schedules at time of quotation and subject to change, based on manufacturing plant loading. 3. Q001.1 : – Exception - To all ISO 9000 requirements. Clarification – Testing is per applicable NEMA/ANSI and UL standards. Cl arification - Witness of GE standard industry production testing is not incl uded add $2500/MCC for the first day straight time. and $1000/MCC for each additional day straight-time and adds 4-5 additional working days to the quoted lead-times. Insp ection of assemblies requires a two week advanced notice and is subject to GE plant restrictions on site. Exception – To any access to GE sub tier suppliers. 4. Q0001.1.5.2 thru .6: Charges for material s and/or labor to remedy a problem with equipment will not be accepted unless prior written approval to remedy said problem has been obtained from GE. (see page 12 para. E). In and out charges are not included. 5. Silicon Rectifier Units field mounted and connected by others. 6. VFD units shown fed from MCC 1C31 and others are remote and by others.

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 14 

### COMMENTS, CLARIFICATIONS, SPECIAL CONDITIONS

1. Cable terminations use mechanical type compression lugs, not (crimp) hydraulic type compression lugs, if crimp type lugs are applied, GE will supply provision for this type of lug by others. (Refer to GE distributors.) Mechanical lugs will accept either copper or aluminum cables (UL CU/AL rated). High vo ltage terminators such as potheads, stress cone, loadbreak and/or deadbreak elbows are not included. (Refer to GE distributors.)

2. Floor channels, threaded bar stock, rubbe r mats, nameplates for any equipment, arc flash labeling, external isomode pads, tran sformer wall mountings, transformer lugs, externally mounted station batteries, racks and chargers are not included unless shown as a separate item within this bill of material. (Refer to GE distributors.)

3. No 600V fuses (except initial limiters for Tr i-Break or AKRU type circuit breakers) are included unless included in the description of the individual piece of equipment or listed as a separate item. When fuses are included in bill of material, no spares or spare fuse cabinets are included. (Refer to GE distributors.)

4. Bi-metal Overload heaters for E9000 Line Motor Control Center starters only are included, but motor nameplate data (full load current, se rvice factor, locked rotor kVA) must be forwarded prior to release for shipment.

5. Unless stipulated in the aforementioned pr oposal, equipment propos ed is finished using GE Products standard application process and ANSI 61 color. Equipment enclosures will be indoor NEMA 1 type unless shown otherwise.



### 6. Coordination/Short Circuit Studies, Arc Flash Studies, field testing, taking field measurements, installation and/or start-up a ssistance by GE Engineering Service or FastTeam partners is not included unless shown as a separate item within this bill of material. When included, they apply to proposed new GE Products only. Refer to GE distributors for per diem rates. GE or GE Fast-Team Field Engineering Service will require contractor provided qualified electricians support.

# g GE Industrial C & I, Jacksonville, Florida SJRPP NOx Reduction Project, Black & Veatch Corp. Prop.# 6F4-291130 Rev-4a, 5/3/2007, GE Supply Co.

“GE Imagination at Work”
© Copyright GE 2007 15 

### TERMS & CONDITIONS SUMMARY

This is a partial listing. The current complete GE terms of sale with A detailed explanation of terms and conditions is available from your GE Distributor.

A. Standard Price Adjustment Clause 1Q - 1. This quotation expires 30 calendar days from its date unless terminated sooner by notice. 2. The prices stated herein are firm provided: a. The order is released, with complete engineering details, for shipment within 90 calendar days from the date of order or at the Company’s earliest convenience thereafter; or b. If drawings for approval are required, the drawings must be returned and approved within 60 calendar days of the original mailing date of the drawings by the Company with products covered by the drawings released for manufacture. Such release must call for shipment within 90 calendar days from the date of order or at the Company’s earliest convenience thereafter. Drawing resubmittals, which are required for any reason other than to correct Company errors, will not extend the 60-day period for release. 3. In the event that the customer for any reason does not comply with the conditions in paragraph 2 above and/or shipment is delayed for any reason not within control of the Company, the price shall be increased 1-1/2% for each full month or fraction thereof that shipment * is thereby delayed after the 90-day period from the date of order.

B. Delivery of this electrical equipment to any common carrier shall constitute delivery to the purchaser; and all risk of loss and damage during shipment shall pass to the purchaser at that time.

C. Freight charges are prepaid and included in the price F.O.B. point of shipment to accessible common carrier point nearest first destination.

D. Standard warranty is applicable for (12) twelve months from date of start-up or (18) eight een months from shipment whichever comes first.

E. Charges for materials and/or labor to remedy a problem with GE equipment will not be accepted unless prior written approval to remedy said problem has been obtained from GE.

F. GE liability is limited in connection with the performance per the "Force Majure" and "Limitation of Liability" limitations of GE selling policy.

G. Order Cancellation - Schedule of Charges: 10%-Order received and entered on factory, work not started, material not ordered. 30%-Engineering completed &/or drawings for approval submitted. 60%-Approved drawings returned. Job released for manufacture and shipment. 80%-Material accumulated and production started. 100%-Manufacturing completed.