Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 02, 2011 Page 1 of 13
Facility Information:

2830_Walter C Beckjord_Unit 5-2

757 US Route 52

New Richmond OH 45157

Contact: Jon Hays

Phone: 317-838-4445

Fax: 317-8382490

Email: jon.hays@duke.energy.com

Testing Company:

AECOM

2 Technology Park Drive

Westford MA 01886

Contact: Patrick Ford

Phone: 978-589-3427

Fax: 978-589-3100

Email: pat.ford@aecom.com

Air Permit Number: Permitted Source ID/Name:

5-1 No. 2 Fuel Oil/Coal-Fired Electric Utility Boiler

Permitted Maximum Process Rate:

971 Million Btu/hour

Max. Normal Operation Process Rate:

971 Million Btu/hour

Target Process Test Rate

971 Million Btu/hour

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

This description should describe the process and associated controls to differentiate this facility from, or document 

similarity with others of same SCC.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 3902500002 FRS #: 10000392888

SCC / Description 10100212 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Tangential) (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 132 120 125.7 4 2 6 30

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 60 0

Stack Exit 2,3,7,8-TCDD Method 23 3 450 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 450 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 450 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 450 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 450 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 450 0

Wednesday, February 02, 2011 Page 2 of 13
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Stack Exit OCDD Method 23 3 450 0

Stack Exit 2,3,7,8-TCDF Method 23 3 450 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 450 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 450 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 450 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 450 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 450 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 450 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 450 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 450 0

Stack Exit OCDF Method 23 3 450 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 450 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 450 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 450 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 450 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 450 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 450 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 450 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 450 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 450 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 450 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 450 0

Wednesday, February 02, 2011 Page 3 of 13
Sampling / Stack Data Results Summary

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 5/5/2010 5/6/2010 5/7/2010

Run Start Time 9:15:00 AM 8:25:00 

AM

7:50:00 AM

Run Finish Time 5:24:00 PM 4:20:00 

PM

3:40:00 PM

Net Run Time, minutes 450 450 450

Dry Gas Meter Volume Sampled, dscf 311.261 323.020 322.243 318.841

Moisture Content of Stack Gas, % 6.80 6.21 7.01 6.673

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.1 10.6 10.8 10.500

Oxygen, % 8 8.7 8.2 8.300

Average Stack Gas Temperature, °F 270.20 265.58 269.68 268.487

Dry Volumetric Flow Rate, dry scfm 365,760.0 383,035.7 378,853.5 375,883.067

Actual Wet Volumetric Flue Gas Flow Rate, acfm 550,836.0 567,864.0 571,824.0 563,508.000

Percent Isokinetic of Sampling Rate, % 100.3 99.4 100.3 100.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 02, 2011 Page 4 of 13
Emissions Summary

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000033 0.000000016 0.000000014 0.000

lb/mmBtuO2 3.70E-12 1.83E-12 1.54E-12 0.000

ug/dscm 3.74E-06 1.75E-06 1.53E-06 0.000

ug/dscm@7%O2 4.03E-06 1.99E-06 1.67E-06 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000089 0.0000000065 0.0000000078 0.000

lb/mmBtuO2 9.99E-13 7.43E-13 8.59E-13 0.000

ug/dscm 1.01E-06 7.11E-07 8.55E-07 0.000

ug/dscm@7%O2 1.09E-06 8.10E-07 9.36E-07 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000061 0.0000000023 0.0000000033 0.000

lb/mmBtuO2 6.85E-13 2.63E-13 3.63E-13 0.000

ug/dscm 6.92E-07 2.51E-07 3.62E-07 0.000

ug/dscm@7%O2 7.46E-07 2.86E-07 3.96E-07 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000067 0.0000000025 0.0000000031 0.000

lb/mmBtuO2 7.52E-13 2.86E-13 3.41E-13 0.000

ug/dscm 7.60E-07 2.73E-07 3.40E-07 0.000

ug/dscm@7%O2 8.19E-07 3.11E-07 3.72E-07 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000074 0.0000000074 0.0000000072 0.000

lb/mmBtuO2 8.30E-13 8.46E-13 7.93E-13 0.000

ug/dscm 8.40E-07 8.09E-07 7.89E-07 0.000

ug/dscm@7%O2 9.05E-07 9.22E-07 8.64E-07 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000065 0.0000000043 0.000000003 0.000

lb/mmBtuO2 7.29E-13 4.92E-13 3.30E-13 0.000

ug/dscm 7.38E-07 4.70E-07 3.29E-07 0.000

ug/dscm@7%O2 7.95E-07 5.35E-07 3.60E-07 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Wednesday, February 02, 2011 Page 5 of 13
RunNumber 1 2 3

Mass_mg 0.0000000064 0.0000000034 0.0000000024 0.000

lb/mmBtuO2 7.18E-13 3.89E-13 2.64E-13 0.000

ug/dscm 7.26E-07 3.72E-07 2.63E-07 0.000

ug/dscm@7%O2 7.82E-07 4.24E-07 2.88E-07 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000066 0.0000000067 0.000000003 0.000

lb/mmBtuO2 7.41E-13 7.66E-13 3.30E-13 0.000

ug/dscm 7.49E-07 7.33E-07 3.29E-07 0.000

ug/dscm@7%O2 8.07E-07 8.35E-07 3.60E-07 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000033 0.0000000018 0.0000000021 0.000

lb/mmBtuO2 3.70E-13 2.06E-13 2.31E-13 0.000

ug/dscm 3.74E-07 1.97E-07 2.30E-07 0.000

ug/dscm@7%O2 4.03E-07 2.24E-07 2.52E-07 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000073 0.0000000036 0.000000004 0.000

lb/mmBtuO2 8.19E-13 4.12E-13 4.40E-13 0.000

ug/dscm 8.28E-07 3.94E-07 4.38E-07 0.000

ug/dscm@7%O2 8.92E-07 4.49E-07 4.79E-07 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000064 0.000000003 0.0000000034 0.000

lb/mmBtuO2 7.18E-13 3.43E-13 3.74E-13 0.000

ug/dscm 7.26E-07 3.28E-07 3.73E-07 0.000

ug/dscm@7%O2 7.82E-07 3.74E-07 4.08E-07 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.000000015 0.0000000123 0.0000000094 0.000

lb/mmBtuO2 1.68E-12 1.41E-12 1.04E-12 0.000

ug/dscm 1.70E-06 1.34E-06 1.03E-06 0.000

ug/dscm@7%O2 1.83E-06 1.53E-06 1.13E-06 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000082 0.000000046 0.000000122 0.000

lb/mmBtuO2 9.20E-12 5.26E-12 1.34E-11 0.000

ug/dscm 9.30E-06 5.03E-06 1.34E-05 0.000

ug/dscm@7%O2 1.00E-05 5.73E-06 1.47E-05 0.000

Wednesday, February 02, 2011 Page 6 of 13
Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000199 0.000000139 0.0000003 0.000

lb/mmBtuO2 2.23E-11 1.59E-11 3.30E-11 0.000

ug/dscm 2.26E-05 1.52E-05 3.29E-05 0.000

ug/dscm@7%O2 2.44E-05 1.73E-05 3.60E-05 0.000

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000179 0.0000000134 0.0000000161 0.000

lb/mmBtuO2 2.01E-12 1.53E-12 1.77E-12 0.000

ug/dscm 2.03E-06 1.47E-06 1.76E-06 0.000

ug/dscm@7%O2 2.19E-06 1.67E-06 1.93E-06 0.000

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000017 0.0000000133 0.0000000102 0.000

lb/mmBtuO2 1.91E-12 1.52E-12 1.12E-12 0.000

ug/dscm 1.93E-06 1.45E-06 1.12E-06 0.000

ug/dscm@7%O2 2.08E-06 1.65E-06 1.23E-06 0.000

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000056 0.00000043 0.00000069 0.000

lb/mmBtuO2 6.28E-11 4.92E-11 7.60E-11 0.000

ug/dscm 6.35E-05 4.70E-05 7.56E-05 0.000

ug/dscm@7%O2 6.84E-05 5.35E-05 8.27E-05 0.000

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000182 0.0000000145 0.000000012 0.000

lb/mmBtuO2 2.04E-12 1.66E-12 1.32E-12 0.000

ug/dscm 2.07E-06 1.59E-06 1.32E-06 0.000

ug/dscm@7%O2 2.23E-06 1.81E-06 1.44E-06 0.000

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000029 0.0000000015 0.0000000026 0.000

lb/mmBtuO2 3.25E-13 1.72E-13 2.86E-13 0.000

ug/dscm 3.29E-07 1.64E-07 2.85E-07 0.000

ug/dscm@7%O2 3.55E-07 1.87E-07 3.12E-07 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000078 0.0000000031 0.0000000035 0.000

lb/mmBtuO2 8.75E-13 3.54E-13 3.85E-13 0.000

Wednesday, February 02, 2011 Page 7 of 13
ug/dscm 8.85E-07 3.39E-07 3.84E-07 0.000

ug/dscm@7%O2 9.54E-07 3.86E-07 4.20E-07 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.0000000069 0.0000000078 0.000

lb/mmBtuO2 1.35E-12 7.89E-13 8.59E-13 0.000

ug/dscm 1.36E-06 7.54E-07 8.55E-07 0.000

ug/dscm@7%O2 1.47E-06 8.59E-07 9.36E-07 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000072 0.000000016 0.000000011 0.000

lb/mmBtuO2 8.08E-13 1.83E-12 1.21E-12 0.000

ug/dscm 8.17E-07 1.75E-06 1.21E-06 0.000

ug/dscm@7%O2 8.80E-07 1.99E-06 1.32E-06 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000192 0.000000015 0.0000000104 0.000

lb/mmBtuO2 2.15E-12 1.72E-12 1.15E-12 0.000

ug/dscm 2.18E-06 1.64E-06 1.14E-06 0.000

ug/dscm@7%O2 2.35E-06 1.87E-06 1.25E-06 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000178 0.0000000147 0.0000000114 0.000

lb/mmBtuO2 2.00E-12 1.68E-12 1.26E-12 0.000

ug/dscm 2.02E-06 1.61E-06 1.25E-06 0.000

ug/dscm@7%O2 2.18E-06 1.83E-06 1.37E-06 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000242 0.0000000189 0.0000000389 0.000

lb/mmBtuO2 2.72E-12 2.16E-12 4.28E-12 0.000

ug/dscm 2.75E-06 2.07E-06 4.26E-06 0.000

ug/dscm@7%O2 2.96E-06 2.36E-06 4.66E-06 0.000

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000241 0.0000000188 0.0000000117 0.000

lb/mmBtuO2 2.70E-12 2.15E-12 1.29E-12 0.000

ug/dscm 2.73E-06 2.06E-06 1.28E-06 0.000

ug/dscm@7%O2 2.94E-06 2.35E-06 1.40E-06 0.000

Compound: OCDD

Average

RunNumber 1 2 3

Wednesday, February 02, 2011 Page 8 of 13
Process Run Data

Mass_mg 0.000000048 0.000000027 0.000000036 0.000

lb/mmBtuO2 5.39E-12 3.09E-12 3.96E-12 0.000

ug/dscm 5.45E-06 2.95E-06 3.95E-06 0.000

ug/dscm@7%O2 5.87E-06 3.36E-06 4.32E-06 0.000

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000017 0.0000000043 0.000000011 0.000

lb/mmBtuO2 1.91E-12 4.92E-13 1.21E-12 0.000

ug/dscm 1.93E-06 4.70E-07 1.21E-06 0.000

ug/dscm@7%O2 2.08E-06 5.35E-07 1.32E-06 0.000

Wednesday, February 02, 2011 Page 9 of 13
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 0 0

2 Heat Input Million Btus/million BTU using O2 0 0

3 Heat Input Million Btus/million BTU using O2 0 0

4 Heat Input Million Btus/million BTU using O2 0 0

1 Average Heat Input 0 MMBtu/hr 0

2 Average Heat Input 0 MMBtu/hr 0

3 Average Heat Input 0 MMBtu/hr 0

4 Average Heat Input 0 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

2 Steam Output 0 1000 lb steam/hr 0

3 Steam Output 0 1000 lb steam/hr 0

4 Steam Output 0 1000 lb steam/hr 0

1 Synfuel Firing Rate 0 1000 Tons/hr 0

2 Synfuel Firing Rate 0 1000 Tons/hr 0

3 Synfuel Firing Rate 0 1000 Tons/hr 0

4 Synfuel Firing Rate 0 1000 Tons/hr 0

1 Petroleum Coke Firing Rate 0 1000 Tons/hr 0

2 Petroleum Coke Firing Rate 0 1000 Tons/hr 0

3 Petroleum Coke Firing Rate 0 1000 Tons/hr 0

4 Petroleum Coke Firing Rate 0 1000 Tons/hr 0

1 Coal Gas Firing Rate 0 Ft^3/min 0

2 Coal Gas Firing Rate 0 Ft^3/min 0

3 Coal Gas Firing Rate 0 Ft^3/min 0

4 Coal Gas Firing Rate 0 Ft^3/min 0

1 Fuel Oil Firing Rate 0 gal/hr 0

2 Fuel Oil Firing Rate 0 gal/hr 0

3 Fuel Oil Firing Rate 0 gal/hr 0

4 Fuel Oil Firing Rate 0 gal/hr 0

1 Flue Gas Flow Rate 0 0

4 Flue Gas Flow Rate 0 0

1 Pressure Drop Across FGD (if applicable) 0 in H20 0

4 Pressure Drop Across FGD (if applicable) 0 in H20 0

1 FGD Scrubber Liquor pH 0 pH 0

Wednesday, February 02, 2011 Page 10 of 13
APCD Run Data

Process Lab Run Data

4 FGD Scrubber Liquor pH 0 pH 0

1 FGD Scrubber Liquor Flow Rate 0 gal/min 0

4 FGD Scrubber Liquor Flow Rate 0 gal/min 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

4 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

1 Flue Gas Oxygen Content 0 % 0

4 Flue Gas Oxygen Content 0 % 0

1 Flue Gas Carbon Dioxide Content 0 % 0

4 Flue Gas Carbon Dioxide Content 0 % 0

1 Flue Gas Moisture Content 0 % 0

4 Flue Gas Moisture Content 0 % 0

1 Flue Gas Sampling Point Temperature 0 Deg F 0

4 Flue Gas Sampling Point Temperature 0 Deg F 0

1 Flue Gas Pressure 0 atm 0

4 Flue Gas Pressure 0 atm 0

1 Standard Pressure 0 atm 0

4 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

4 Standard Temperature 0 Deg F 0

1 Unit Gross Electrical Output 0 Mwe 0

4 Unit Gross Electrical Output 0 Mwe 0

1 Unit Net Electric Generation 0 MWh 0

4 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

Target

Value

1 List all emissions control devices in order of 

process flow. Choose from

0 0

1 drop down lists. If not on list add description and 

provide detailed

0 0

1 desription in section 5a. 0 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

Wednesday, February 02, 2011 Page 11 of 13
1 Ultimate/Proximate Analysis 0

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Wednesday, February 02, 2011 Page 12 of 13
Sampling / Stack Data Results Detail

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 5/5/2010 5/6/2010 5/7/2010

Run Start Time 9:15:00 AM 8:25:00 AM 7:50:00 AM

Run Finish Time 5:24:00 PM 4:20:00 PM 3:40:00 PM

Net Traversing Points 60 60 60

Net Run Time, minutes 450 450 450

Nozzle Diameter, inches 0.195 0.195 0.195 0.195

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.016 1.016 1.016 1.016

Barometric Pressure, inches of Mercury 29.3 29.4 29.25 29.317

Average Orifice Meter Differential, inches H2O 1.63 1.74 1.75 1.707

Dry Gas Meter Volume Sampled, cubic feet 318.253 325.956 327.937 324.049

Average Dry Gas Meter Temperature, °F 79.33 74.23 76.05 76.537

Dry Gas Meter Volume Sampled, dscf 311.261 323.020 322.243 318.841

Total Moisture Liquid collected, g 482.3 454.6 516 484.300

Volume of Water Vapor, standard cubic feet 22.70 21.40 24.29 22.797

Moisture Content of Stack Gas, % 6.80 6.21 7.01 6.673

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.932 0.9379 0.9299 0.933

Carbon Dioxide, % 10.1 10.6 10.8 10.500

Oxygen, % 8 8.7 8.2 8.300

Carbon Monoxide & Nitrogen, % 81.9 80.7 81 81.200

Fuel Factor 1.28 1.15 1.18

Dry Molecular Weight, lb/lb-Mole 29.94 30.04 30.06 30.013

Wet Molecular weight, lb/lb-Mole 29.13 29.29 29.21 29.210

Flue Gas Static Pressure, inches of H2O 2.4 2.3 2.8 2.500

Absolute Flue Gas Pressure, inches of Mercury 29.48 29.57 29.46 29.503

Average Stack Gas Temperature, °F 270.20 265.58 269.68 268.487

Average Velocity Head, inches of H2O 1.5886040840

3775

1.713550664

81216

1.716783219

19098

1.673

Average Stack Gas Velocity, feet/second 83.46 86.04 86.64 85.380

Stack Cross-Sectional Area, square feet 110.000 110.000 110.000 110.000

Dry Volumetric Flow Rate, dry scfm 365,760.0 383,035.7 378,853.5 375,883.067

Actual Wet Volumetric Flue Gas Flow Rate, acfm 550,836.0 567,864.0 571,824.0 563,508.000

Percent Isokinetic of Sampling Rate, % 100.3 99.4 100.3 100.000

Percent Excess Air, % 58.7 69.0 62.2 63.300

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches

Rectangular Duct Width, inches 120 120 120

Rectangular Duct Length, inches 132 132 132

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 02, 2011 Page 13 of 13