Name:

Title:

Company:

Sign Date:

Name: Mike Taylor

Title: President

Company: Catalyst Air Management

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

KY6041 Spurlock Unit 4

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 21, 2011 Page 1 of 17
KY6041 Spurlock Unit 4

Facility Information:

Spurlock

1301 West 2nd st.

Maysville KY 41056

Contact: Louis Petrey

Phone: 859-745-4157 ext. 204

Fax:

Email: louis.petrey@ekpc.coop

Testing Company:

Catalyst Air Management

2505 Byington-Solway Rd

Knoxville TN 37931

Contact:Mike Taylor

Phone: 865-531-0075

Fax: 831-531-0750

Email: mike.taylor@catalystair.com

Air Permit Number:

6041

Permitted Source ID/Name:

4 Hugh L. Spurlock Generating Station

Permitted Maximum Process Rate:

2800 mmBtu/hr

Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Spurlock Unit 4 is a coal-fired circulating fluidized bed (CFB) steam generating utility boiler located near Maysville, 

KY. The unit is equipped with a baghouse, flash dryer absorber, and SNCR for PM, SO2 and Nox control.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110017429521 FRS #: 110017429521

SCC / Description 10100218 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Atmospheric Fluidized Bed Combustion: Circulating Bed (Bitum. Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

KY6041 

Spulock Unit 4

176.1 0 0 0 1608 5232 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

KY6041 Carbon Monoxide Method 10 3 120 0

Spulock Unit 4

KY6041 Formaldehyde Method 0011 3 120 0

Spulock Unit 4

Total organic compounds 

(TOC) as Propane

KY6041 Method 25A 3 120 0

Spulock Unit 4

Monday, February 21, 2011 Page 2 of 17
KY6041 Spurlock Unit 4

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

KY6041 Hydrogen Chloride Method 26A 3 180 0

Spulock Unit 4

KY6041 Hydrogen Fluoride Method 26A 3 180 0

Spulock Unit 4

KY6041 Chlorine Method 26A 3 180 0

Spulock Unit 4

KY6041 Filterable PM2.5 OTM - 27/28 3 369 0

Spulock Unit 4

KY6041 Total PM2.5 OTM - 27/28 3 369 0

Spulock Unit 4

Organic Condensible 

Particulate

KY6041 OTM - 27/28 3 369 0

Spulock Unit 4

Inorganic (Aqueous) 

Condensible Part.

KY6041 OTM - 27/28 3 369 0

Spulock Unit 4

KY6041 Manganese Method 29 3 240 0

Spulock Unit 4

KY6041 Nickel Method 29 3 240 0

Spulock Unit 4

KY6041 Lead Method 29 3 240 0

Spulock Unit 4

KY6041 Cobalt Method 29 3 240 0

Spulock Unit 4

KY6041 Chromium Method 29 3 240 0

Spulock Unit 4

KY6041 Cadmium Method 29 3 240 0

Spulock Unit 4

KY6041 Beryllium Method 29 3 240 0

Spulock Unit 4

KY6041 Antimony Method 29 3 240 0

Spulock Unit 4

KY6041 Arsenic Method 29 3 240 0

Spulock Unit 4

KY6041 Filterable Particulate Method 29 3 240 0

Spulock Unit 4

KY6041 Selenium Method 29 3 240 0

Spulock Unit 4

Monday, February 21, 2011 Page 3 of 17
KY6041 Spurlock Unit 4

Sampling / Stack Data Results Summary

Location KY6041 Spulock Unit 4 - Method 0011

Average

Run Number M0011-1 M0011-2 M0011-3

Test Date 3/25/2010 3/25/2010 3/25/2010

Run Start Time 7:04:00 AM 9:44:00 

AM

12:30:00 PM

Run Finish Time 9:19:00 AM 11:59:00 

AM

2:45:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 77.782 78.638 79.205 78.542

Moisture Content of Stack Gas, % 10.93 11.09 11.01 11.010

Moisture Saturation at Stack Gas Temperature, % 49.28 49.19 49.47 49.313

Carbon Dioxide, % 14.4 14.4 14.4 14.400

Oxygen, % 5.2 5 5.1 5.100

Average Stack Gas Temperature, °F 176.75 176.67 176.92 176.780

Dry Volumetric Flow Rate, dry scfm 534,617.4 540,566.7 542,210.0 539,131.367

Actual Wet Volumetric Flue Gas Flow Rate, acfm 751,996.4 761,637.4 763,565.6 759,066.467

Percent Isokinetic of Sampling Rate, % 104.2 104.1 104.6 104.300

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location KY6041 Spulock Unit 4 - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 21, 2011 Page 4 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location KY6041 Spulock Unit 4 - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 21, 2011 Page 5 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location KY6041 Spulock Unit 4 - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 21, 2011 Page 6 of 17
KY6041 Spurlock Unit 4

Emissions Summary

Location: KY6041 Spulock Unit 4 - Method 0011

Compound: Formaldehyde

Average

RunNumber M0011-1 M0011-2 M0011-3

Mass_mg 0.006 0.004 0.003 0.004

lb/mmBtuO2 2.21E-06 1.44E-06 1.08E-06 0.000

ppm 2.18E-03 1.44E-03 1.07E-03 0.002

ppm@7%O2 1.93E-03 1.26E-03 9.41E-04 0.001

Location: KY6041 Spulock Unit 4 - Method 10

Compound: Carbon Monoxide

Average

Run M10-1 M10-2 M10-3

lb/mmBtuO2 5.36E-02 5.58E-02 5.21E-02 0.054

ppm 5.66E+01 5.78E+01 5.54E+01 56.600

ppm@7%O2 5.01E+01 5.22E+01 4.87E+01 50.333

Location: KY6041 Spulock Unit 4 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run M25A-1 M25A-2 M25A-3

lb/mmBtuO2 1.32E-04 6.75E-05 3.36E-04 0.000

ppm 8.84E-02 4.44E-02 2.27E-01 0.120

ppm@7%O2 7.83E-02 4.01E-02 2.00E-01 0.106

Location: KY6041 Spulock Unit 4 - Method 26A

Compound: Chlorine

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 1.2 1.2 1.2 1.200

lb/mmBtuO2 2.93E-04 2.84E-04 2.96E-04 0.000

Compound: Hydrogen Chloride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 0.54 0.52 0.55 0.537

lb/mmBtuO2 1.32E-04 1.23E-04 1.36E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 0.2 0.2 0.2 0.200

lb/mmBtuO2 4.89E-05 4.73E-05 4.94E-05 0.000

Location: KY6041 Spulock Unit 4 - Method 29

Compound: Antimony

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00245 0.0018 0.0018 0.002

Monday, February 21, 2011 Page 7 of 17
KY6041 Spurlock Unit 4

lb/mmBtuO2 4.61E-07 3.36E-07 3.40E-07 0.000

Compound: Arsenic

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00245 0.00181 0.00194 0.002

lb/mmBtuO2 4.61E-07 3.38E-07 3.67E-07 0.000

Compound: Beryllium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00045 0.00045 0.00045 0.000

lb/mmBtuO2 8.47E-08 8.40E-08 8.51E-08 0.000

Compound: Cadmium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0007 0.00055 0.00045 0.001

lb/mmBtuO2 1.32E-07 1.03E-07 8.51E-08 0.000

Compound: Chromium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00869 0.00813 0.00726 0.008

lb/mmBtuO2 1.64E-06 1.52E-06 1.37E-06 0.000

Compound: Cobalt

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00287 0.00325 0.00087 0.002

lb/mmBtuO2 5.40E-07 6.07E-07 1.64E-07 0.000

Compound: Filterable Particulate

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 24 39.6 35.6 33.067

lb/mmBtuO2 4.52E-03 7.39E-03 6.73E-03 0.006

Compound: Lead

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.01643 0.02051 0.01616 0.018

lb/mmBtuO2 3.09E-06 3.83E-06 3.05E-06 0.000

Compound: Manganese

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0086 0.0074 0.0093 0.008

lb/mmBtuO2 1.62E-06 1.38E-06 1.76E-06 0.000

Compound: Nickel

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0084 0.006 0.0067 0.007

Monday, February 21, 2011 Page 8 of 17
KY6041 Spurlock Unit 4

Process Run Data

lb/mmBtuO2 1.58E-06 1.12E-06 1.27E-06 0.000

Compound: Selenium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0073 0.0055 0.0045 0.006

lb/mmBtuO2 1.37E-06 1.03E-06 8.51E-07 0.000

Location: KY6041 Spulock Unit 4 - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 19.76 13.76 16.96 16.827

lb/mmBtuO2 6.23E-03 3.30E-03 3.91E-03 0.004

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 40 67 82 63.000

lb/mmBtuO2 1.26E-02 1.61E-02 1.89E-02 0.016

Compound: Organic Condensible Particulate

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 2.7 2.3 2.4 2.467

lb/mmBtuO2 8.51E-04 5.52E-04 5.54E-04 0.001

Compound: Total PM2.5

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 62.46 83.06 101.36 82.293

lb/mmBtuO2 1.97E-02 1.99E-02 2.34E-02 0.021

Monday, February 21, 2011 Page 9 of 17
KY6041 Spurlock Unit 4

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Unit Load 299.8 MW 0 March 18, 2010

1 Steam Rate 2030 1000 lbs/hr 0 March 18, 2010

1 Heat Input 2621 mmBtu/hr 0 March 18, 2010

4 Unit Load 299.8 MW 0 March 23, 2010

4 Steam Rate 2033 1000 lbs/hr 0 March 23, 2010

4 Heat Input 2584 mmBtu/hr 0 March 23, 2010

5 Unit Load 299.8 MW 0 March 24, 2010

5 Steam Rate 2033 1000 lbs/hr 0 March 24, 2010

5 Heat Input 2632 mmBtu/hr 0 March 24, 2010

6 Unit Load 299.8 MW 0 March 25, 2010

6 Steam Rate 2033 1000 lbs/hr 0 March 25, 2010

6 Heat Input 2611 mmBtu/hr 0 March 25, 2010

1 Bituminous Coal Burned Tons/million BTU using O2 0 0

Run Name Value UOM Comments

Target

Value

1 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

186.5 lbs/hr 0

2 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

187.7 lbs/hr 0

3 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

214.29 lbs/hr 0

4 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

228.1 lbs/hr 0

1 FLUID BED DRY SCRUBBER 78.44 1000 lbs/hr 0

2 FLUID BED DRY SCRUBBER 83.16 1000 lbs/hr 0

3 FLUID BED DRY SCRUBBER 102.52 1000 lbs/hr 0

4 FLUID BED DRY SCRUBBER 94.43 1000 lbs/hr 0

1 BAGHOUSE 5.63 in. H2O 0

2 BAGHOUSE 5.76 in. H2O 0

3 BAGHOUSE 5.59 in. H2O 0

4 BAGHOUSE 5.54 in. H2O 0

Run Name Value UOM Comments

Monday, February 21, 2011 Page 10 of 17
KY6041 Spurlock Unit 4

Run Name Value UOM Comments

1 0

Monday, February 21, 2011 Page 11 of 17
KY6041 Spurlock Unit 4

Sampling / Stack Data Results Detail

Location KY6041 Spulock Unit 4 - Method 0011

Average

Run Number M0011-1 M0011-2 M0011-3

Test Date 3/25/2010 3/25/2010 3/25/2010

Run Start Time 7:04:00 AM 9:44:00 AM 12:30:00 PM

Run Finish Time 9:19:00 AM 11:59:00 AM 2:45:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.19 0.19 0.19 0.190

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.01 1.01 1.01 1.010

Barometric Pressure, inches of Mercury 28.9 28.9 28.9 28.900

Average Orifice Meter Differential, inches H2O 1.25 1.30 1.31 1.287

Dry Gas Meter Volume Sampled, cubic feet 79.107 80.722 81.576 80.468

Average Dry Gas Meter Temperature, °F 65.54 70.50 72.29 69.443

Dry Gas Meter Volume Sampled, dscf 77.782 78.638 79.205 78.542

Total Moisture Liquid collected, g 202.6 208.5 208.2 206.433

Volume of Water Vapor, standard cubic feet 9.54 9.81 9.80 9.717

Moisture Content of Stack Gas, % 10.93 11.09 11.01 11.010

Moisture Saturation at Stack Gas Temperature, % 49.28 49.19 49.47 49.313

Dry Mole Fraction 0.8907 0.8891 0.8899 0.890

Carbon Dioxide, % 14.4 14.4 14.4 14.400

Oxygen, % 5.2 5 5.1 5.100

Carbon Monoxide & Nitrogen, % 80.4 80.6 80.5 80.500

Fuel Factor 1.09 1.10 1.10

Dry Molecular Weight, lb/lb-Mole 30.51 30.50 30.51 30.507

Wet Molecular weight, lb/lb-Mole 29.14 29.11 29.13 29.127

Flue Gas Static Pressure, inches of H2O -1.4 -1.4 -1.4 -1.400

Absolute Flue Gas Pressure, inches of Mercury 28.80 28.80 28.80 28.800

Average Stack Gas Temperature, °F 176.75 176.67 176.92 176.780

Average Velocity Head, inches of H2O 1.4032918141

1412

1.438242585

75181

1.446034240

94866

1.429

Average Stack Gas Velocity, feet/second 74.10 75.05 75.24 74.797

Stack Cross-Sectional Area, square feet 169.140 169.140 169.140 169.140

Dry Volumetric Flow Rate, dry scfm 534,617.4 540,566.7 542,210.0 539,131.367

Actual Wet Volumetric Flue Gas Flow Rate, acfm 751,996.4 761,637.4 763,565.6 759,066.467

Percent Isokinetic of Sampling Rate, % 104.2 104.1 104.6 104.300

Percent Excess Air, % 32.4 30.7 31.6 31.567

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 176.1 176.1 176.1

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 12 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 21, 2011 Page 13 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 21, 2011 Page 14 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 21, 2011 Page 15 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 21, 2011 Page 16 of 17
KY6041 Spurlock Unit 4

Location KY6041 Spulock Unit 4 - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 21, 2011 Page 17 of 17