### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date



## Electrical Utilites MACT Information Collection Request Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Friday, March 04, 2011 Page 1 of 20

### Electrical Utilites MACT Information Collection Request

Facility Information: Cogentrix Scrubgrass Generating

2151 Lisbon Road

Kennerdell PA 16374
Contact: Richard J. Shaffer
Phone: 814-385-6661 ex. 28
Fax: 814-385-6704
Email: RichardShaffer@Cogentrix.com Testing Company: Blue Mountain Environmental Management Corpora 1191 Pittsburgh Road

Valencia PA 16059
Contact: Alex Keffalas
Phone: 724-898-4500
Fax: 724-898-2908
Email: akeffalas@bluemountainusa.com

Air Permit Number:
61-00181 Permitted Source ID/Name:
SCRUBGRASS POWER CORP 94-3128347-1
Permitted Maximum Process Rate:
828000 lbs/hr steam Max. Normal Operation Process Rate:
808000 lbs/hr steam Target Process Test Rate
808000 lbs/hr steam

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 4242100025 FRS #: 2211

SCC / Description 10102018 External Combustion Boilers - Electric Generation - Waste Coal - Circulating Fluidized Bed Combustion

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
Emission Stack 129 1080 2700 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Flowrate Method 1 - 4 3 60 0 Emission Stack % H2O Method 1 - 4 3 60 0 Emission Stack Carbon Monoxide Method 10 3 120 0 Emission Stack Formaldehyde Method 0011 3 120 0 Emission Stack Total organic compounds

(TOC) as Methane Method 25A 3 120 0 Emission Stack

Hydrogen Fluoride Method 26A 3 60 0 Emission Stack Hydrogen Chloride Method 26A 3 60 0 Emission Stack



### Friday, March 04, 2011 Page 2 of 20

### Electrical Utilites MACT Information Collection Request

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

See Paul Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 247 0 Emission Stack

Filterable PM2.5 OTM - 27/28 0 Emission Stack Organic Condensible

Particulate OTM - 27/28 3 247 0 Emission Stack

Nickel Method 29 3 180 0 Emission Stack Manganese Method 29 3 180 0 Emission Stack Lead Method 29 3 180 0 Emission Stack Chromium Method 29 3 180 0 Emission Stack Cobalt Method 29 3 180 0 Emission Stack Cadmium Method 29 3 180 0 Emission Stack Beryllium Method 29 3 180 0 Emission Stack Antimony Method 29 3 180 0 Emission Stack Arsenic Method 29 3 180 0 Emission Stack Selenium Method 29 3 180 0 Emission Stack Filterable Particulate Method 5 3 180 0 Emission Stack Sulfur Dioxide Method 6C 3 60 0 Emission Stack Nitrogen oxides (NOx) Method 7E 3 60 0 Emission Stack



### Friday, March 04, 2011 Page 3 of 20

### Electrical Utilites MACT Information Collection Request

Sampling / Stack Data Results Summary



### Location Emission Stack - Method 10 Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Location Emission Stack - Method 25A Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Friday, March 04, 2011 Page 4 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 26A Average
Run Number 1 2 3

Test Date 3/23/2010 3/23/2010 3/23/2010
Run Start Time 2:16:00 PM 3:30:00 PM 4:45:00 PM
Run Finish Time 3:22:00 PM 4:36:00 PM 5:51:00 PM Net Run Time, minutes 60 60 60 Dry Gas Meter Volume Sampled, dscf 42.459 42.383 41.833 42.225 Moisture Content of Stack Gas, % 10.14 10.36 11.17 10.557 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.8 14.7 14.5 14.667 Oxygen, % 4.7 4.8 4.9 4.800 Average Stack Gas Temperature, °F 306.92 306.33 309.58 307.610 Dry Volumetric Flow Rate, dry scfm 245,365.8 243,710.9 243,762.1 244,279.600 Actual Wet Volumetric Flue Gas Flow Rate, acfm 424,716.4 420,305.3 426,785.8 423,935.833 Percent Isokinetic of Sampling Rate, % 101.0 101.5 100.2 100.900 F-Factor, dscfm/MMBtu @ %O2 10137 10148 10378 10,221.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000



### Location Emission Stack - Method 29 Average
Run Number

Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2

Fw

Fc



### Friday, March 04, 2011 Page 5 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 5 Average
Run Number

Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2

Fw

Fc



### Location Emission Stack - Method 6C Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Friday, March 04, 2011 Page 6 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 7E Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Location Emission Stack - OTM - 27/28 Average
Run Number

Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2

Fw

Fc



### Friday, March 04, 2011 Page 7 of 20

### Electrical Utilites MACT Information Collection Request

Emissions Summary



### Location: Emission Stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 Elb/hr 5.40E+01 5.17E+01 5.20E+01 52.567 lb/mmBtuO2 4.64E-02 4.50E-02 4.56E-02 0.046
ppm 5.05E+01 4.87E+01 4.91E+01 49.433 ppm@7%O2 4.33E+01 4.20E+01 4.27E+01 42.667



### Location: Emission Stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 Elb/hr 2.00E-01 1.62E-01 1.29E-01 0.164 lb/mmBtuO2 1.72E-04 1.41E-04 1.11E-04 0.000
ppm 3.26E-01 2.66E-01 2.10E-01 0.267 ppm@7%O2 2.81E-01 2.30E-01 1.80E-01 0.230



### Location: Emission Stack - Method 26A Compound: Hydrogen Chloride Average RunNumber 1 2 3 Mass_mg 110 108 114 110.667 Elb/hr 8.41E+01 8.21E+01 8.79E+01 84.700 lb/mmBtuO2 7.47E-02 7.40E-02 8.14E-02 0.077
ppm 6.04E+01 5.94E+01 6.35E+01 61.100


### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 76 72 76 74.667 Elb/hr 5.81E+01 5.48E+01 5.86E+01 57.167 lb/mmBtuO2 5.16E-02 4.93E-02 5.43E-02 0.052
ppm 7.60E+01 7.21E+01 7.71E+01 75.067



### Location: Emission Stack - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.004 0.004 0.004 0.004 Elb/hr 6.49E-04 5.87E-04 5.84E-04 0.001 gr/dscf 3.12E-07 2.76E-07 2.63E-07 0.000 lb/mmBtuO2 5.84E-07 5.01E-07 4.86E-07 0.000


### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.0505 0.0391 0.0293 0.040 Elb/hr 8.19E-03 5.74E-03 4.27E-03 0.006 gr/dscf 3.94E-06 2.70E-06 1.93E-06 0.000



### Friday, March 04, 2011 Page 8 of 20

### Electrical Utilites MACT Information Collection Request

lb/mmBtuO2 7.38E-06 4.90E-06 3.56E-06 0.000


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.00125 0.0013 0.00121 0.001 Elb/hr 2.03E-04 1.91E-04 1.77E-04 0.000 gr/dscf 9.75E-08 8.99E-08 7.96E-08 0.000 lb/mmBtuO2 1.83E-07 1.63E-07 1.47E-07 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.02311 0.01191 0.00548 0.014 Elb/hr 3.75E-03 1.75E-03 7.99E-04 0.002 gr/dscf 1.80E-06 8.23E-07 3.60E-07 0.000 lb/mmBtuO2 3.38E-06 1.49E-06 6.66E-07 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.0254 0.0265 0.0207 0.024 Elb/hr 4.12E-03 3.89E-03 3.02E-03 0.004 gr/dscf 1.98E-06 1.83E-06 1.36E-06 0.000 lb/mmBtuO2 3.71E-06 3.32E-06 2.52E-06 0.000


### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.00655 0.00431 0.00395 0.005 Elb/hr 1.06E-03 6.32E-04 5.76E-04 0.001 gr/dscf 5.11E-07 2.98E-07 2.60E-07 0.000 lb/mmBtuO2 9.57E-07 5.40E-07 4.80E-07 0.000


### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.0923 0.0303 0.0172 0.047 Elb/hr 1.50E-02 4.45E-03 2.51E-03 0.007 gr/dscf 7.20E-06 2.09E-06 1.13E-06 0.000 lb/mmBtuO2 1.35E-05 3.79E-06 2.09E-06 0.000


### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.08 0.0713 0.1665 0.106 Elb/hr 1.30E-02 1.05E-02 2.43E-02 0.016 gr/dscf 6.24E-06 4.93E-06 1.10E-05 0.000 lb/mmBtuO2 1.17E-05 8.93E-06 2.02E-05 0.000


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.024 0.0272 0.0151 0.022



### Friday, March 04, 2011 Page 9 of 20

### Electrical Utilites MACT Information Collection Request

Elb/hr 3.89E-03 3.99E-03 2.20E-03 0.003 gr/dscf 1.87E-06 1.88E-06 9.93E-07 0.000 lb/mmBtuO2 3.51E-06 3.41E-06 1.83E-06 0.000


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0106 10 0.01 3.340 Elb/hr 1.72E-03 1.47E+00 1.46E-03 0.491 gr/dscf 8.26E-07 6.91E-04 6.58E-07 0.000 lb/mmBtuO2 1.55E-06 1.25E-03 1.22E-06 0.000



### Location: Emission Stack - Method 5 Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 219.33 223.74 231.5 224.857 Elb/hr 3.56E+01 3.28E+01 3.38E+01 34.067 gr/dscf 1.71E-02 1.55E-02 1.52E-02 0.016 lb/mmBtuO2 3.20E-02 2.80E-02 2.81E-02 0.029



### Location: Emission Stack - Method 6C 

### Compound: Sulfur Dioxide Average Run 1 2 3 Elb/hr 4.39E+02 4.17E+02 4.14E+02 423.333 lb/mmBtuO2 3.77E-01 3.63E-01 3.63E-01 0.368
ppm 1.80E+02 1.72E+02 1.71E+02 174.333 ppm@7%O2 1.54E+02 1.48E+02 1.49E+02 150.333



### Location: Emission Stack - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 1 2 3 Elb/hr 1.75E+02 1.50E+02 1.48E+02 157.667 lb/mmBtuO2 1.50E-01 1.31E-01 1.30E-01 0.137
ppm 9.95E+01 8.62E+01 8.52E+01 90.300 ppm@7%O2 8.54E+01 7.44E+01 7.40E+01 77.933



### Location: Emission Stack - OTM - 27/28 Compound: Filterable PM2.5 Average RunNumber 1 3 2 Mass_mg 15.05 6.75 12.1 11.300 Elb/hr 6.45E+00 2.88E+00 4.91E+00 4.747 gr/dscf 2.85E-03 1.26E-03 2.10E-03 0.002 lb/mmBtuO2 5.34E-03 2.34E-03 3.81E-03 0.004


### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber 1 3 2 Mass_mg 11 9.9 12 10.967



### Friday, March 04, 2011 Page 10 of 20

### Electrical Utilites MACT Information Collection Request

Process Run Data Elb/hr 4.71E+00 4.22E+00 4.87E+00 4.600 gr/dscf 2.08E-03 1.85E-03 2.09E-03 0.002 lb/mmBtuO2 3.90E-03 3.43E-03 3.78E-03 0.004


### Compound: Organic Condensible Particulate Average RunNumber 1 3 2 Mass_mg 2.5 1.1 2.5 2.033 Elb/hr 1.07E+00 4.69E-01 1.01E+00 0.850 gr/dscf 4.73E-04 2.06E-04 4.34E-04 0.000 lb/mmBtuO2 8.87E-04 3.81E-04 7.87E-04 0.001



### Friday, March 04, 2011 Page 11 of 20

### Electrical Utilites MACT Information Collection Request

Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value
1 Average Heat Input 0 mmBtu/hr 0



### 1 0 /hr 0

2 Average Heat Input 0 mmBtu/hr 0

2 0 /hr 0



### 3 Average Heat Input 0 mmBtu/hr 0

3 0 /hr 0

4 Average Heat Input 0 mmBtu/hr 0



### 4 0 /hr 0

5 Average Heat Input 0 mmBtu/hr 0

5 0 /hr 0



### 6 Average Heat Input 0 mmBtu/hr 0

6 0 /hr 0

Run Name Value UOM Comments Target Value


### 1 BAGHOUSE 0 0

Friday, March 04, 2011 Page 12 of 20

### Electrical Utilites MACT Information Collection Request

Sampling / Stack Data Results Detail



### Location Emission Stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, March 04, 2011 Page 13 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, March 04, 2011 Page 14 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 26A Average Run Number 1 2 3 Test Date 3/23/2010 3/23/2010 3/23/2010 Run Start Time 2:16:00 PM 3:30:00 PM 4:45:00 PM Run Finish Time 3:22:00 PM 4:36:00 PM 5:51:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 60 60 60 Nozzle Diameter, inches 0.218 0.218 0.218 0.218 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.994 0.994 0.994 0.994 Barometric Pressure, inches of Mercury 28.05 28.2 28.15 28.133 Average Orifice Meter Differential, inches H2O 1.88 1.89 1.93 1.900 Dry Gas Meter Volume Sampled, cubic feet 44.502 44.364 44.212 44.359 Average Dry Gas Meter Temperature, °F 58.25 60.33 64.50 61.027 Dry Gas Meter Volume Sampled, dscf 42.459 42.383 41.833 42.225 Total Moisture Liquid collected, g 101.7 104.2 111.8 105.900 Volume of Water Vapor, standard cubic feet 4.79 4.90 5.26 4.983 Moisture Content of Stack Gas, % 10.14 10.36 11.17 10.557 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8986 0.8964 0.8883 0.894 Carbon Dioxide, % 14.8 14.7 14.5 14.667 Oxygen, % 4.7 4.8 4.9 4.800 Carbon Monoxide & Nitrogen, % 80.5 80.5 80.6 80.533 Fuel Factor 1.09 1.10 1.10 Dry Molecular Weight, lb/lb-Mole 30.56 30.54 30.52 30.540 Wet Molecular weight, lb/lb-Mole 29.29 29.24 29.12 29.217 Flue Gas Static Pressure, inches of H2O -1.5 -1.5 -1.5 -1.500 Absolute Flue Gas Pressure, inches of Mercury 27.94 28.09 28.04 28.023 Average Stack Gas Temperature, °F 306.92 306.33 309.58 307.610 Average Velocity Head, inches of H2O 1.2585891215 297 1.238068137

2841 1.263792677

46172 1.253

Average Stack Gas Velocity, feet/second 77.99 77.18 78.37 77.847 Stack Cross-Sectional Area, square feet 90.763 90.763 90.763 90.763 Dry Volumetric Flow Rate, dry scfm 245,365.8 243,710.9 243,762.1 244,279.600 Actual Wet Volumetric Flue Gas Flow Rate, acfm 424,716.4 420,305.3 426,785.8 423,935.833 Percent Isokinetic of Sampling Rate, % 101.0 101.5 100.2 100.900 Percent Excess Air, % 28.4 29.2 29.9 29.167 F-Factor, dscfm/MMBtu @ %O2 10137 10148 10378 10,221.000 Round Duct Diameter, inches 129 129 129 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 0 0 0 0.000 Fc 0 0 0 0.000



### Friday, March 04, 2011 Page 15 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, March 04, 2011 Page 16 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 5 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, March 04, 2011 Page 17 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, March 04, 2011 Page 18 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, March 04, 2011 Page 19 of 20

### Electrical Utilites MACT Information Collection Request

Location Emission Stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, March 04, 2011 Page 20 of 20