Name: C. D. Holley

Title: Vice President F&H System Operation

Company: Dominion Generation

Sign Date: 7/2/2010

Name: Michael P. Martin

Title: Senior Project Manager

Company: TRC Companies, Inc.

Sign Date: 7/1/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, January 13, 2011 Page 1 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Facility Information:

Mt Storm

State Route 93

Mount Storm W 26739

Contact: David Nuckols

Phone: 804-796-6021

Fax: 804-796-6004

Email: david.nuckols@dom.com

Testing Company:

TRC Companies, Inc.

650 Suffolk Street

Lowell MA 01854

Contact:Michael P. Martin

Phone: 978-656-3550

Fax: 978-453-4215

Email: mmartin@trcsolutions.com

Air Permit Number:

3954

Permitted Source ID/Name:

1_2

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 1 & Unit 2 are each a 6000 mmBtu/hr tangentially fired, pulverized coal boiler. Each have LNB w/ overfire air, 

SCR, a wet limestone FGD, & an ESP which vent to a common stack.

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 5402300003 FRS #: 110007876637

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 465.6 0 0 0 1728 5868 4 6

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Thursday, January 13, 2011 Page 2 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Thursday, January 13, 2011 Page 3 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 4/13/2010 4/14/2010 4/14/2010

Run Start Time

Run Finish Time

Net Run Time, minutes 192 192 192

Dry Gas Meter Volume Sampled, dscf 120.049 120.052 123.513 121.205

Moisture Content of Stack Gas, % 14.94 15.36 14.62 14.973

Moisture Saturation at Stack Gas Temperature, % 12.63 12.51 12.62 12.587

Carbon Dioxide, % 12.58 12.56 12.56 12.567

Oxygen, % 6.81 6.9 6.74 6.817

Average Stack Gas Temperature, °F 119.88 119.67 120.00 119.850

Dry Volumetric Flow Rate, dry scfm 2,788,491.3 2,784,044.2 2,855,588.5 2,809,374.66

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,861,383.9 3,834,425.9 3,938,710.9 3,878,173.56

7

Percent Isokinetic of Sampling Rate, % 101.4 101.5 101.8 101.567

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 13, 2011 Page 4 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 13, 2011 Page 5 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Emissions Summary

Process Run Data

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 3 2

Mass_mg 1.29 1.34 2.13 1.587

lb/mmBtuO2 3.44E-04 3.45E-04 5.71E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 3 2

Mass_mg 0.572 3.25 0.263 1.362

lb/mmBtuO2 1.52E-04 8.37E-04 7.05E-05 0.000

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 8.61E-02 1.11E-01 1.06E-01 0.101

ppm 3.57E+01 4.58E+01 4.43E+01 41.933

ppm@7%O2 3.52E+01 4.55E+01 4.35E+01 41.400

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 7.14E-02 6.91E-02 6.94E-02 0.070

ppm 4.13E+01 3.97E+01 4.03E+01 40.433

ppm@7%O2 4.07E+01 3.94E+01 3.95E+01 39.867

Thursday, January 13, 2011 Page 6 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Unit 1 & 2 Combined Total Heat Input 10202 Million Btus/hr Collected during 

M26A Run 1

0

1 Unit 1 Flue Gas Oxygen Content 3.501 % Collected during 

M26A Run 1

0

1 Unit 1 & 2 Combined Total Coal Firing Rate 0.4168 1,000 Tons/hr Collected during 

M26A Run 1

0

1 Unit 1 & 2 Combined Total Steam Output 7479.61,000 lbs steam/hr Collected during 

M26A Run 1

0

1 Unit 1 & 2 Combined Total Flue Gas Flow Rate 4E+06 dscfm Collected during 

M26A Run 1

0

1 Flue Gas Sampling Point Temperature 117.3 Deg F Collected during 

M26A Run 1

0

1 Unit 2 Flue Gas Oxygen Content 3.506 % Collected during 

M26A Run 1

0

1 Flue Gas Carbon Dioxide Content 11.061 % Collected during 

M26A Run 1

0

1 Unit 2 Fuel Oil Firing Rate 0.0053 Gal/hr Collected during 

M26A Run 1

0

2 Unit 1 & 2 Combined Total Heat Input 10203 Million Btus/hr Collected during 

M26A Run 2

0

2 Unit 1 Flue Gas Oxygen Content 3.508 % Collected during 

M26A Run 2

0

2 Unit 1 & 2 Combined Total Coal Firing Rate 0.4168 1,000 Tons/hr Collected during 

M26A Run 2

0

2 Unit 1 & 2 Combined Total Steam Output 7476.71,000 lbs steam/hr Collected during 

M26A Run 2

0

2 Unit 1 & 2 Combined Total Flue Gas Flow Rate 4E+06 dscfm Collected during 

M26A Run 2

0

2 Flue Gas Sampling Point Temperature 117.28 Deg F Collected during 

M26A Run 2

0

2 Unit 2 Flue Gas Oxygen Content 3.524 % Collected during 

M26A Run 2

0

2 Flue Gas Carbon Dioxide Content 11.036 % Collected during 

M26A Run 2

0

2 Unit 2 Fuel Oil Firing Rate 0.0025 Gal/hr Collected during 

M26A Run 2

0

3 Unit 1 & 2 Combined Total Heat Input 10198 Million Btus/hr Collected during 

M26A Run 3

0

3 Unit 1 Flue Gas Oxygen Content 3.504 % Collected during 

M26A Run 3

0

3 Unit 1 & 2 Combined Total Coal Firing Rate 10198 1,000 Tons/hr Collected during 

M26A Run 3

0

Thursday, January 13, 2011 Page 7 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

3 Unit 1 & 2 Combined Total Steam Output 7473.31,000 lbs steam/hr Collected during 

M26A Run 3

0

3 Unit 1 & 2 Combined Total Flue Gas Flow Rate 4E+06 dscfm Collected during 

M26A Run 3

0

3 Flue Gas Sampling Point Temperature 117.93 Deg F Collected during 

M26A Run 3

0

3 Unit 2 Flue Gas Oxygen Content 3.489 % Collected during 

M26A Run 3

0

3 Flue Gas Carbon Dioxide Content 10.979 % Collected during 

M26A Run 3

0

3 Unit 2 Fuel Oil Firing Rate 0.0051 Gal/hr Collected during 

M26A Run 3

0

4 Unit 1 & 2 Combined Total Heat Input 10202 Million Btus/hr Collected during 

Run 1 of Method 

6C and 7E

0

4 Unit 1 Flue Gas Oxygen Content 3.497 % Collected during 

Run 1 of Method 

6C and 7E

0

4 Unit 1 & 2 Combined Total Coal Firing Rate 0.4168 1,000 Tons/hr Collected during 

Run 1 of Method 

6C and 7E

0

4 Unit 1 & 2 Combined Total Steam Output 7479.61,000 lbs steam/hr Collected during 

Run 1 of Method 

6C and 7E

0

4 Unit 1 & 2 Combined Total Flue Gas Flow Rate 4E+06 dscfm Collected during 

Run 1 of Method 

6C and 7E

0

4 Flue Gas Sampling Point Temperature 117.37 Deg F Collected during 

Run 1 of Method 

6C and 7E

0

4 Unit 2 Flue Gas Oxygen Content 3.507 % Collected during 

Run 1 of Method 

6C and 7E

0

4 Flue Gas Carbon Dioxide Content 11.06 % Collected during 

Run 1 of Method 

6C and 7E

0

4 Unit 2 Fuel Oil Firing Rate 0.0067 Gal/hr Collected during 

Run 1 of Method 

6C and 7E

0

5 Unit 1 & 2 Combined Total Heat Input 10205 Million Btus/hr Collected during 

Run 2 of Method 

6C and 7E

0

5 Unit 1 Flue Gas Oxygen Content 3.509 % Collected during 

Run 2 of Method 

6C and 7E

0

5 Unit 1 & 2 Combined Total Coal Firing Rate 0.4169 1,000 Tons/hr Collected during 

Run 2 of Method 

6C and 7E

0

Thursday, January 13, 2011 Page 8 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

APCD Run Data

5 Unit 1 & 2 Combined Total Steam Output 7476.71,000 lbs steam/hr Collected during 

Run 2 of Method 

6C and 7E

0

5 Unit 1 & 2 Combined Total Flue Gas Flow Rate 4E+06 dscfm Collected during 

Run 2 of Method 

6C and 7E

0

5 Flue Gas Sampling Point Temperature 117.20 Deg F Collected during 

Run 2 of Method 

6C and 7E

0

5 Unit 2 Flue Gas Oxygen Content 3.53 % Collected during 

Run 2 of Method 

6C and 7E

0

5 Flue Gas Carbon Dioxide Content 11.066 % Collected during 

Run 2 of Method 

6C and 7E

0

5 Unit 2 Fuel Oil Firing Rate 0.0032 Gal/hr Collected during 

Run 2 of Method 

6C and 7E

0

6 Unit 1 & 2 Combined Total Heat Input 110199 Million Btus/hr Collected during 

Run 3 of Method 

6C and 7E

0

6 Unit 1 Flue Gas Oxygen Content 3.504 % Collected during 

Run 3 of Method 

6C and 7E

0

6 Unit 1 & 2 Combined Total Coal Firing Rate 0.4166 1,000 Tons/hr Collected during 

Run 3 of Method 

6C and 7E

0

6 Unit 1 & 2 Combined Total Steam Output 7473.31,000 lbs steam/hr Collected during 

Run 3 of Method 

6C and 7E

0

6 Unit 1 & 2 Combined Total Flue Gas Flow Rate 4E+06 dscfm Collected during 

Run 3 of Method 

6C and 7E

0

6 Flue Gas Sampling Point Temperature 117.92 Deg F Collected during 

Run 3 of Method 

6C and 7E

0

6 Unit 2 Flue Gas Oxygen Content 3.49 % Collected during 

Run 3 of Method 

6C and 7E

0

6 Flue Gas Carbon Dioxide Content 10.968 % Collected during 

Run 3 of Method 

6C and 7E

0

6 Unit 2 Fuel Oil Firing Rate 0.0064 Gal/hr Collected during 

Run 3 of Method 

6C and 7E

0

Target

Value

Thursday, January 13, 2011 Page 9 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 OVERFIRE AIR 0 0

1 LOW NOX BURNERS 0 0

1 SCR (SELECTIVE CATALYTIC REDUCTION) 0 0

1 WET SCRUBBER 0 0

1 ELECTROSTATIC PRECIPITATOR 0 0

Thursday, January 13, 2011 Page 10 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 4/13/2010 4/14/2010 4/14/2010

Run Start Time

Run Finish Time

Net Traversing Points 48 48 48

Net Run Time, minutes 192 192 192

Nozzle Diameter, inches 0.219 0.219 0.219 0.219

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9965 0.9965 0.9965 0.997

Barometric Pressure, inches of Mercury 27.1 27.2 27.2 27.167

Average Orifice Meter Differential, inches H2O 1.41 1.41 1.48 1.433

Dry Gas Meter Volume Sampled, cubic feet 131.509 131.980 135.940 133.143

Average Dry Gas Meter Temperature, °F 64.05 67.85 68.55 66.817

Dry Gas Meter Volume Sampled, dscf 120.049 120.052 123.513 121.205

Total Moisture Liquid collected, g 448 462.7 449.4 453.367

Volume of Water Vapor, standard cubic feet 21.09 21.78 21.15 21.340

Moisture Content of Stack Gas, % 14.94 15.36 14.62 14.973

Moisture Saturation at Stack Gas Temperature, % 12.63 12.51 12.62 12.587

Dry Mole Fraction 0.8737 0.8749 0.8738 0.874

Carbon Dioxide, % 12.58 12.56 12.56 12.567

Oxygen, % 6.81 6.9 6.74 6.817

Carbon Monoxide & Nitrogen, % 80.61 80.54 80.7 80.617

Fuel Factor 1.12 1.11 1.13

Dry Molecular Weight, lb/lb-Mole 30.29 30.29 30.28 30.287

Wet Molecular weight, lb/lb-Mole 29.15 29.27 29.09 29.170

Flue Gas Static Pressure, inches of H2O 0.78 0.76 0.91 0.817

Absolute Flue Gas Pressure, inches of Mercury 27.16 27.26 27.27 27.230

Average Stack Gas Temperature, °F 119.88 119.67 120.00 119.850

Average Velocity Head, inches of H2O 0.7844757825

69369

0.779906338

680959

0.817491426

282948

0.794

Average Stack Gas Velocity, feet/second 54.43 54.05 55.52 54.667

Stack Cross-Sectional Area, square feet 1,182.370 1,182.370 1,182.370 1,182.370

Dry Volumetric Flow Rate, dry scfm 2,788,491.3 2,784,044.2 2,855,588.5 2,809,374.6

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,861,383.9 3,834,425.9 3,938,710.9 3,878,173.5

67

Percent Isokinetic of Sampling Rate, % 101.4 101.5 101.8 101.567

Percent Excess Air, % 47.1 48.0 46.3 47.133

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 465.6 465.6 465.6

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Thursday, January 13, 2011 Page 11 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 12 of 13
Utility Boiler MACT ICR - Mt Storm Power Station Units 1 & 2

7/2/2010

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 13 of 13