Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Electrical Utilites MACT Information Collection Request

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, March 04, 2011 Page 1 of 20
Electrical Utilites MACT Information Collection Request

Facility Information:

Cogentrix Scrubgrass Generating

2151 Lisbon Road

Kennerdell PA 16374

Contact: Richard J. Shaffer

Phone: 814-385-6661 ex. 28

Fax: 814-385-6704

Email: RichardShaffer@Cogentrix.com

Testing Company:

Blue Mountain Environmental Management Corpora

1191 Pittsburgh Road

Valencia PA 16059

Contact: Alex Keffalas

Phone: 724-898-4500

Fax: 724-898-2908

Email: akeffalas@bluemountainusa.com

Air Permit Number:

61-00181

Permitted Source ID/Name:

94-3128347-1 SCRUBGRASS POWER CORP

Permitted Maximum Process Rate:

828000 lbs/hr steam

Max. Normal Operation Process Rate:

808000 lbs/hr steam

Target Process Test Rate

808000 lbs/hr steam

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4242100025 FRS #: 2211

SCC / Description 10102018 External Combustion Boilers - Electric Generation - Waste Coal - Circulating 

Fluidized Bed Combustion 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Emission Stack 129 0 0 0 1080 2700 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Emission Stack Flowrate Method 1 - 4 3 60 0

Emission Stack % H2O Method 1 - 4 3 60 0

Emission StackCarbon Monoxide Method 10 3 120 0

Emission Stack Formaldehyde Method 0011 3 120 0

Total organic compounds 

(TOC) as Methane

Emission Stack Method 25A 3 120 0

Emission StackHydrogen Fluoride Method 26A 3 60 0

Emission StackHydrogen Chloride Method 26A 3 60 0

Friday, March 04, 2011 Page 2 of 20
Electrical Utilites MACT Information Collection Request

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

See Paul

Inorganic (Aqueous) 

Condensible Part.

Emission Stack OTM - 27/28 3 247 0

Emission Stack Filterable PM2.5 OTM - 27/28 0

Organic Condensible 

Particulate

Emission Stack OTM - 27/28 3 247 0

Emission StackNickel Method 29 3 180 0

Emission StackManganese Method 29 3 180 0

Emission StackLead Method 29 3 180 0

Emission StackChromium Method 29 3 180 0

Emission StackCobalt Method 29 3 180 0

Emission StackCadmium Method 29 3 180 0

Emission StackBeryllium Method 29 3 180 0

Emission StackAntimony Method 29 3 180 0

Emission StackArsenic Method 29 3 180 0

Emission Stack Selenium Method 29 3 180 0

Emission Stack Filterable Particulate Method 5 3 180 0

Emission Stack Sulfur Dioxide Method 6C 3 60 0

Emission StackNitrogen oxides (NOx) Method 7E 3 60 0

Friday, March 04, 2011 Page 3 of 20
Electrical Utilites MACT Information Collection Request

Sampling / Stack Data Results Summary

Location Emission Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Emission Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, March 04, 2011 Page 4 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 26A

Average

Run Number 1 2 3

Test Date 3/23/2010 3/23/2010 3/23/2010

Run Start Time 2:16:00 PM 3:30:00 PM 4:45:00 PM

Run Finish Time 3:22:00 PM 4:36:00 PM 5:51:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 42.459 42.383 41.833 42.225

Moisture Content of Stack Gas, % 10.14 10.36 11.17 10.557

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14.8 14.7 14.5 14.667

Oxygen, % 4.7 4.8 4.9 4.800

Average Stack Gas Temperature, °F 306.92 306.33 309.58 307.610

Dry Volumetric Flow Rate, dry scfm 245,365.8 243,710.9 243,762.1 244,279.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 424,716.4 420,305.3 426,785.8 423,935.833

Percent Isokinetic of Sampling Rate, % 101.0 101.5 100.2 100.900

F-Factor, dscfm/MMBtu @ %O2 10137 10148 10378 10,221.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Emission Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Friday, March 04, 2011 Page 5 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Emission Stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, March 04, 2011 Page 6 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Emission Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Friday, March 04, 2011 Page 7 of 20
Electrical Utilites MACT Information Collection Request

Emissions Summary

Location: Emission Stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

Elb/hr 5.40E+01 5.17E+01 5.20E+01 52.567

lb/mmBtuO2 4.64E-02 4.50E-02 4.56E-02 0.046

ppm 5.05E+01 4.87E+01 4.91E+01 49.433

ppm@7%O2 4.33E+01 4.20E+01 4.27E+01 42.667

Location: Emission Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 2.00E-01 1.62E-01 1.29E-01 0.164

lb/mmBtuO2 1.72E-04 1.41E-04 1.11E-04 0.000

ppm 3.26E-01 2.66E-01 2.10E-01 0.267

ppm@7%O2 2.81E-01 2.30E-01 1.80E-01 0.230

Location: Emission Stack - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 110 108 114 110.667

Elb/hr 8.41E+01 8.21E+01 8.79E+01 84.700

lb/mmBtuO2 7.47E-02 7.40E-02 8.14E-02 0.077

ppm 6.04E+01 5.94E+01 6.35E+01 61.100

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 76 72 76 74.667

Elb/hr 5.81E+01 5.48E+01 5.86E+01 57.167

lb/mmBtuO2 5.16E-02 4.93E-02 5.43E-02 0.052

ppm 7.60E+01 7.21E+01 7.71E+01 75.067

Location: Emission Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.004 0.004 0.004 0.004

Elb/hr 6.49E-04 5.87E-04 5.84E-04 0.001

gr/dscf 3.12E-07 2.76E-07 2.63E-07 0.000

lb/mmBtuO2 5.84E-07 5.01E-07 4.86E-07 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.0505 0.0391 0.0293 0.040

Elb/hr 8.19E-03 5.74E-03 4.27E-03 0.006

gr/dscf 3.94E-06 2.70E-06 1.93E-06 0.000

Friday, March 04, 2011 Page 8 of 20
Electrical Utilites MACT Information Collection Request

lb/mmBtuO2 7.38E-06 4.90E-06 3.56E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00125 0.0013 0.00121 0.001

Elb/hr 2.03E-04 1.91E-04 1.77E-04 0.000

gr/dscf 9.75E-08 8.99E-08 7.96E-08 0.000

lb/mmBtuO2 1.83E-07 1.63E-07 1.47E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.02311 0.01191 0.00548 0.014

Elb/hr 3.75E-03 1.75E-03 7.99E-04 0.002

gr/dscf 1.80E-06 8.23E-07 3.60E-07 0.000

lb/mmBtuO2 3.38E-06 1.49E-06 6.66E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0254 0.0265 0.0207 0.024

Elb/hr 4.12E-03 3.89E-03 3.02E-03 0.004

gr/dscf 1.98E-06 1.83E-06 1.36E-06 0.000

lb/mmBtuO2 3.71E-06 3.32E-06 2.52E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00655 0.00431 0.00395 0.005

Elb/hr 1.06E-03 6.32E-04 5.76E-04 0.001

gr/dscf 5.11E-07 2.98E-07 2.60E-07 0.000

lb/mmBtuO2 9.57E-07 5.40E-07 4.80E-07 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0923 0.0303 0.0172 0.047

Elb/hr 1.50E-02 4.45E-03 2.51E-03 0.007

gr/dscf 7.20E-06 2.09E-06 1.13E-06 0.000

lb/mmBtuO2 1.35E-05 3.79E-06 2.09E-06 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.08 0.0713 0.1665 0.106

Elb/hr 1.30E-02 1.05E-02 2.43E-02 0.016

gr/dscf 6.24E-06 4.93E-06 1.10E-05 0.000

lb/mmBtuO2 1.17E-05 8.93E-06 2.02E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.024 0.0272 0.0151 0.022

Friday, March 04, 2011 Page 9 of 20
Electrical Utilites MACT Information Collection Request

Elb/hr 3.89E-03 3.99E-03 2.20E-03 0.003

gr/dscf 1.87E-06 1.88E-06 9.93E-07 0.000

lb/mmBtuO2 3.51E-06 3.41E-06 1.83E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0106 10 0.01 3.340

Elb/hr 1.72E-03 1.47E+00 1.46E-03 0.491

gr/dscf 8.26E-07 6.91E-04 6.58E-07 0.000

lb/mmBtuO2 1.55E-06 1.25E-03 1.22E-06 0.000

Location: Emission Stack - Method 5

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 219.33 223.74 231.5 224.857

Elb/hr 3.56E+01 3.28E+01 3.38E+01 34.067

gr/dscf 1.71E-02 1.55E-02 1.52E-02 0.016

lb/mmBtuO2 3.20E-02 2.80E-02 2.81E-02 0.029

Location: Emission Stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

Elb/hr 4.39E+02 4.17E+02 4.14E+02 423.333

lb/mmBtuO2 3.77E-01 3.63E-01 3.63E-01 0.368

ppm 1.80E+02 1.72E+02 1.71E+02 174.333

ppm@7%O2 1.54E+02 1.48E+02 1.49E+02 150.333

Location: Emission Stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Elb/hr 1.75E+02 1.50E+02 1.48E+02 157.667

lb/mmBtuO2 1.50E-01 1.31E-01 1.30E-01 0.137

ppm 9.95E+01 8.62E+01 8.52E+01 90.300

ppm@7%O2 8.54E+01 7.44E+01 7.40E+01 77.933

Location: Emission Stack - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 3 2

Mass_mg 15.05 6.75 12.1 11.300

Elb/hr 6.45E+00 2.88E+00 4.91E+00 4.747

gr/dscf 2.85E-03 1.26E-03 2.10E-03 0.002

lb/mmBtuO2 5.34E-03 2.34E-03 3.81E-03 0.004

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 3 2

Mass_mg 11 9.9 12 10.967

Friday, March 04, 2011 Page 10 of 20
Electrical Utilites MACT Information Collection Request

Process Run Data

Elb/hr 4.71E+00 4.22E+00 4.87E+00 4.600

gr/dscf 2.08E-03 1.85E-03 2.09E-03 0.002

lb/mmBtuO2 3.90E-03 3.43E-03 3.78E-03 0.004

Compound: Organic Condensible Particulate

Average

RunNumber 1 3 2

Mass_mg 2.5 1.1 2.5 2.033

Elb/hr 1.07E+00 4.69E-01 1.01E+00 0.850

gr/dscf 4.73E-04 2.06E-04 4.34E-04 0.000

lb/mmBtuO2 8.87E-04 3.81E-04 7.87E-04 0.001

Friday, March 04, 2011 Page 11 of 20
Electrical Utilites MACT Information Collection Request

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Average Heat Input 0 mmBtu/hr 0

1 0 /hr 0

2 Average Heat Input 0 mmBtu/hr 0

2 0 /hr 0

3 Average Heat Input 0 mmBtu/hr 0

3 0 /hr 0

4 Average Heat Input 0 mmBtu/hr 0

4 0 /hr 0

5 Average Heat Input 0 mmBtu/hr 0

5 0 /hr 0

6 Average Heat Input 0 mmBtu/hr 0

6 0 /hr 0

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 0 0

Friday, March 04, 2011 Page 12 of 20
Electrical Utilites MACT Information Collection Request

Sampling / Stack Data Results Detail

Location Emission Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, March 04, 2011 Page 13 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, March 04, 2011 Page 14 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 26A

Average

Run Number 1 2 3

Test Date 3/23/2010 3/23/2010 3/23/2010

Run Start Time 2:16:00 PM 3:30:00 PM 4:45:00 PM

Run Finish Time 3:22:00 PM 4:36:00 PM 5:51:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.218 0.218 0.218 0.218

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.994 0.994 0.994 0.994

Barometric Pressure, inches of Mercury 28.05 28.2 28.15 28.133

Average Orifice Meter Differential, inches H2O 1.88 1.89 1.93 1.900

Dry Gas Meter Volume Sampled, cubic feet 44.502 44.364 44.212 44.359

Average Dry Gas Meter Temperature, °F 58.25 60.33 64.50 61.027

Dry Gas Meter Volume Sampled, dscf 42.459 42.383 41.833 42.225

Total Moisture Liquid collected, g 101.7 104.2 111.8 105.900

Volume of Water Vapor, standard cubic feet 4.79 4.90 5.26 4.983

Moisture Content of Stack Gas, % 10.14 10.36 11.17 10.557

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8986 0.8964 0.8883 0.894

Carbon Dioxide, % 14.8 14.7 14.5 14.667

Oxygen, % 4.7 4.8 4.9 4.800

Carbon Monoxide & Nitrogen, % 80.5 80.5 80.6 80.533

Fuel Factor 1.09 1.10 1.10

Dry Molecular Weight, lb/lb-Mole 30.56 30.54 30.52 30.540

Wet Molecular weight, lb/lb-Mole 29.29 29.24 29.12 29.217

Flue Gas Static Pressure, inches of H2O -1.5 -1.5 -1.5 -1.500

Absolute Flue Gas Pressure, inches of Mercury 27.94 28.09 28.04 28.023

Average Stack Gas Temperature, °F 306.92 306.33 309.58 307.610

Average Velocity Head, inches of H2O 1.2585891215

297

1.238068137

2841

1.263792677

46172

1.253

Average Stack Gas Velocity, feet/second 77.99 77.18 78.37 77.847

Stack Cross-Sectional Area, square feet 90.763 90.763 90.763 90.763

Dry Volumetric Flow Rate, dry scfm 245,365.8 243,710.9 243,762.1 244,279.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 424,716.4 420,305.3 426,785.8 423,935.833

Percent Isokinetic of Sampling Rate, % 101.0 101.5 100.2 100.900

Percent Excess Air, % 28.4 29.2 29.9 29.167

F-Factor, dscfm/MMBtu @ %O2 10137 10148 10378 10,221.000

Round Duct Diameter, inches 129 129 129

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, March 04, 2011 Page 15 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, March 04, 2011 Page 16 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, March 04, 2011 Page 17 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, March 04, 2011 Page 18 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, March 04, 2011 Page 19 of 20
Electrical Utilites MACT Information Collection Request

Location Emission Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, March 04, 2011 Page 20 of 20