Vienna

Emission Report

NRG

Unit: 8

Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 09:00:01 09:00:59 1 6.8 10.9 616.6 198.4 17.202/24/10 02/24/10 09:01:02 09:01:59 1 6.8 10.9 617.8 199.0 16.502/24/10 02/24/10 09:02:02 09:02:57 1 6.8 11.0 619.8 198.9 22.202/24/10 02/24/10 09:03:00 09:03:58 1 6.8 11.0 618.9 199.0 23.002/24/10 02/24/10 09:04:01 09:04:59 1 6.9 10.9 616.0 199.0 17.202/24/10 02/24/10 09:05:02 09:05:59 1 6.9 10.9 615.8 198.6 22.002/24/10 02/24/10 09:06:02 09:06:57 1 6.9 10.8 613.1 199.2 27.402/24/10 02/24/10 09:07:00 09:07:58 1 6.9 10.8 612.6 199.7 27.602/24/10 02/24/10 09:08:01 09:08:59 1 6.9 10.9 612.7 199.4 27.602/24/10 02/24/10 09:09:02 09:09:59 1 6.9 10.9 614.8 199.2 26.002/24/10 02/24/10 09:10:03 09:10:57 1 6.9 10.9 614.7 198.7 26.402/24/10 02/24/10 09:11:00 09:11:58 1 6.8 10.9 616.1 199.0 27.602/24/10 02/24/10 09:12:01 09:12:59 1 6.8 11.0 617.9 199.0 23.502/24/10 02/24/10 09:13:02 09:13:57 1 6.8 11.0 617.8 199.1 25.302/24/10 02/24/10 09:14:00 09:14:57 1 6.8 10.9 615.9 199.6 25.202/24/10 02/24/10 09:15:00 09:15:58 1 6.9 10.9 615.9 199.5 22.602/24/10 02/24/10 09:16:01 09:16:59 1 6.9 11.0 624.6 200.7 15.802/24/10 02/24/10 09:17:02 09:17:57 1 6.9 11.0 626.6 202.3 11.802/24/10 02/24/10 09:18:00 09:18:57 1 6.9 11.0 626.7 202.5 19.702/24/10 02/24/10 09:19:00 09:19:58 1 6.8 11.0 629.9 203.0 19.202/24/10 02/24/10 09:20:01 09:20:57 1 6.8 11.1 633.4 203.0 15.302/24/10 02/24/10 09:21:00 09:21:57 1 6.8 11.1 634.5 203.0 16.402/24/10 02/24/10 09:22:01 09:22:58 1 6.8 11.1 633.0 203.1 17.802/24/10 02/24/10 09:23:01 09:23:59 1 6.8 11.1 632.5 202.9 19.702/24/10 02/24/10 09:24:02 09:24:57 1 6.9 11.0 630.9 202.6 19.802/24/10 02/24/10 09:25:00 09:25:58 1 6.9 11.0 630.2 202.5 13.502/24/10 02/24/10 09:26:01 09:26:58 1 6.9 11.0 629.6 202.7 17.902/24/10 02/24/10 09:27:02 09:27:59 1 6.9 11.0 628.2 203.3 21.602/24/10 02/24/10 09:28:02 09:28:57 1 6.9 11.0 629.8 203.5 20.502/24/10 02/24/10 09:29:00 09:29:58 1 6.8 11.1 633.6 203.6 23.402/24/10 02/24/10 09:30:01 09:30:59 1 6.8 11.1 634.0 203.1 20.1
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 09:31:02 09:31:59 1 6.8 11.0 634.4 203.1 21.902/24/10 02/24/10 09:32:02 09:32:57 1 6.9 11.0 632.1 202.8 24.402/24/10 02/24/10 09:33:00 09:33:58 1 6.9 11.0 633.1 202.5 25.002/24/10 02/24/10 09:34:01 09:34:59 1 6.9 11.0 631.4 202.8 27.902/24/10 02/24/10 09:35:02 09:35:59 1 6.9 10.9 632.9 202.8 27.402/24/10 02/24/10 09:36:03 09:36:57 1 6.8 11.0 635.7 203.1 28.502/24/10 02/24/10 09:37:00 09:37:58 1 6.8 11.0 636.5 203.5 28.202/24/10 02/24/10 09:38:01 09:38:59 1 6.8 11.0 636.3 203.6 29.902/24/10 02/24/10 09:39:02 09:39:57 1 6.8 11.0 639.6 204.0 31.802/24/10 02/24/10 09:40:00 09:40:57 1 6.8 11.0 638.1 203.3 36.202/24/10 02/24/10 09:41:00 09:41:58 1 6.8 11.0 638.6 203.3 37.702/24/10 02/24/10 09:42:01 09:42:59 1 6.9 10.9 635.4 203.8 36.502/24/10 02/24/10 09:43:02 09:43:57 1 6.9 10.9 635.1 202.9 33.602/24/10 02/24/10 09:44:00 09:44:57 1 6.9 10.9 634.1 203.8 34.302/24/10 02/24/10 09:45:01 09:45:58 1 6.9 11.0 633.3 203.1 35.402/24/10 02/24/10 09:46:01 09:46:59 1 6.8 11.0 636.8 202.8 32.702/24/10 02/24/10 09:47:02 09:47:57 1 6.8 11.0 636.5 203.4 31.202/24/10 02/24/10 09:48:00 09:48:58 1 6.8 11.0 638.2 203.2 33.102/24/10 02/24/10 09:49:01 09:49:58 1 6.8 11.0 635.9 203.6 34.802/24/10 02/24/10 09:50:01 09:50:59 1 6.8 11.0 634.6 204.2 33.502/24/10 02/24/10 09:51:02 09:51:57 1 6.8 11.0 635.1 204.1 34.602/24/10 02/24/10 09:52:00 09:52:58 1 6.9 11.0 633.0 203.7 36.002/24/10 02/24/10 09:53:01 09:53:59 1 6.9 11.0 632.4 203.5 34.402/24/10 02/24/10 09:54:02 09:54:56 1 6.8 11.0 634.3 203.4 37.002/24/10 02/24/10 09:55:00 09:55:57 1 6.8 11.0 636.3 203.4 36.302/24/10 02/24/10 09:56:00 09:56:58 1 6.8 11.0 638.1 203.8 34.602/24/10 02/24/10 09:57:01 09:57:59 1 6.9 11.0 638.5 203.5 35.102/24/10 02/24/10 09:58:02 09:58:57 1 6.8 11.0 639.0 203.4 45.702/24/10 02/24/10 09:59:00 09:59:57 1 6.9 11.0 637.7 203.7 44.602/24/10 02/24/10 10:00:01 10:00:58 1 6.9 11.0 637.2 203.8 44.802/24/10 02/24/10 10:01:01 10:01:59 1 6.9 10.9 636.3 203.1 45.302/24/10 02/24/10 10:02:02 10:02:57 1 6.9 11.0 636.5 203.5 45.402/24/10 02/24/10 10:03:00 10:03:58 1 6.9 11.0 637.2 203.0 46.102/24/10 02/24/10 10:04:01 10:04:58 1 6.9 11.0 638.4 203.3 44.502/24/10 02/24/10 10:05:01 10:05:59 1 6.9 10.9 639.7 203.1 47.802/24/10 02/24/10 10:06:02 10:06:57 1 6.8 11.0 641.5 203.0 45.202/24/10 02/24/10 10:07:00 10:07:58 1 6.8 11.0 639.9 203.5 39.2
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 10:08:01 10:08:59 1 6.8 11.0 636.9 203.5 41.102/24/10 02/24/10 10:09:02 10:09:59 1 6.9 10.9 636.4 203.9 48.402/24/10 02/24/10 10:10:02 10:10:57 1 6.9 10.9 636.1 203.9 43.702/24/10 02/24/10 10:11:00 10:11:58 1 7.0 10.8 632.6 203.7 42.202/24/10 02/24/10 10:12:01 10:12:59 1 7.0 10.8 631.9 203.2 45.502/24/10 02/24/10 10:13:02 10:13:57 1 6.9 10.8 635.1 203.7 45.402/24/10 02/24/10 10:14:00 10:14:58 1 6.9 10.9 636.8 203.8 45.402/24/10 02/24/10 10:15:01 10:15:58 1 6.8 10.9 638.3 203.8 44.602/24/10 02/24/10 10:16:01 10:16:59 1 6.8 11.0 641.1 204.5 42.202/24/10 02/24/10 10:17:02 10:17:57 1 6.8 10.9 640.5 204.2 46.302/24/10 02/24/10 10:18:00 10:18:58 1 6.8 10.9 638.7 204.1 42.002/24/10 02/24/10 10:19:01 10:19:59 1 6.9 10.8 637.7 204.1 45.102/24/10 02/24/10 10:20:02 10:20:59 1 6.9 10.8 633.9 204.3 42.402/24/10 02/24/10 10:21:02 10:21:57 1 6.9 10.8 635.0 204.1 41.502/24/10 02/24/10 10:22:00 10:22:58 1 6.9 10.8 636.3 204.5 43.102/24/10 02/24/10 10:23:01 10:23:59 1 6.8 10.9 638.9 204.6 39.702/24/10 02/24/10 10:24:02 10:24:59 1 6.9 10.9 639.2 204.5 39.902/24/10 02/24/10 10:25:03 10:25:57 1 6.8 10.9 639.8 204.6 41.202/24/10 02/24/10 10:26:00 10:26:58 1 6.9 10.8 637.8 204.4 42.702/24/10 02/24/10 10:27:01 10:27:59 1 6.9 10.8 636.9 204.2 39.002/24/10 02/24/10 10:28:02 10:28:57 1 7.0 10.8 635.9 204.1 43.902/24/10 02/24/10 10:29:00 10:29:58 1 7.0 10.8 635.0 204.0 39.202/24/10 02/24/10 10:30:01 10:30:58 1 7.0 10.8 635.7 203.9 39.502/24/10 02/24/10 10:31:02 10:31:59 1 6.9 10.8 636.9 203.6 43.002/24/10 02/24/10 10:32:02 10:32:57 1 6.8 10.9 641.2 203.3 44.402/24/10 02/24/10 10:33:00 10:33:58 1 6.8 10.9 642.5 204.0 44.502/24/10 02/24/10 10:34:01 10:34:59 1 6.9 10.9 642.8 204.1 43.902/24/10 02/24/10 10:35:02 10:35:59 1 6.8 10.9 644.6 203.7 44.502/24/10 02/24/10 10:36:03 10:36:57 1 6.9 10.8 642.6 204.0 43.202/24/10 02/24/10 10:37:00 10:37:58 1 6.9 10.8 641.4 204.0 42.402/24/10 02/24/10 10:38:01 10:38:59 1 7.0 10.8 639.9 204.0 45.002/24/10 02/24/10 10:39:02 10:39:57 1 7.0 10.8 640.9 204.0 43.602/24/10 02/24/10 10:40:00 10:40:57 1 6.9 10.8 643.1 204.1 47.802/24/10 02/24/10 10:41:00 10:41:58 1 6.8 10.9 647.0 204.0 45.502/24/10 02/24/10 10:42:01 10:42:59 1 6.8 11.0 648.3 204.1 45.702/24/10 02/24/10 10:43:02 10:43:57 1 6.8 11.0 648.8 204.5 45.802/24/10 02/24/10 10:44:00 10:44:58 1 6.8 11.0 648.7 204.6 44.5
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 10:45:01 10:45:58 1 6.8 10.9 648.4 204.3 44.102/24/10 02/24/10 10:46:01 10:46:59 1 6.9 10.9 646.6 204.5 43.502/24/10 02/24/10 10:47:02 10:47:57 1 6.9 10.8 645.2 204.3 47.202/24/10 02/24/10 10:48:00 10:48:58 1 6.9 10.9 645.1 204.2 56.302/24/10 02/24/10 10:49:01 10:49:58 1 6.8 10.9 646.9 204.1 60.102/24/10 02/24/10 10:50:02 10:50:59 1 6.8 10.9 649.1 205.4 58.702/24/10 02/24/10 10:51:02 10:51:57 1 6.7 11.0 651.6 207.1 59.902/24/10 02/24/10 10:52:00 10:52:58 1 6.7 11.0 652.7 207.1 53.902/24/10 02/24/10 10:53:01 10:53:59 1 6.7 11.0 653.1 207.1 55.702/24/10 02/24/10 10:54:02 10:54:57 1 6.8 11.0 652.2 207.6 55.902/24/10 02/24/10 10:55:00 10:55:57 1 6.8 11.0 651.3 207.9 44.202/24/10 02/24/10 10:56:00 10:56:58 1 6.8 10.9 648.9 207.6 54.502/24/10 02/24/10 10:57:01 10:57:59 1 6.9 10.9 649.1 207.7 55.702/24/10 02/24/10 10:58:02 10:58:57 1 6.9 10.9 649.1 207.9 49.902/24/10 02/24/10 10:59:00 10:59:58 1 6.8 10.9 650.5 207.6 51.502/24/10 02/24/10 11:00:01 11:00:58 1 6.8 10.9 651.9 208.1 39.302/24/10 02/24/10 11:01:01 11:01:59 1 6.8 11.0 652.8 208.1 36.302/24/10 02/24/10 11:02:02 11:02:57 1 6.8 11.0 653.3 208.1 38.802/24/10 02/24/10 11:03:00 11:03:58 1 6.8 11.0 651.9 208.5 33.902/24/10 02/24/10 11:04:01 11:04:59 1 6.9 10.9 649.9 208.5 32.902/24/10 02/24/10 11:05:02 11:05:59 1 6.9 10.9 647.9 208.5 41.602/24/10 02/24/10 11:06:02 11:06:57 1 6.9 10.8 646.6 208.4 37.602/24/10 02/24/10 11:07:00 11:07:58 1 6.9 10.8 648.3 208.3 41.902/24/10 02/24/10 11:08:01 11:08:59 1 6.8 10.9 650.4 208.1 44.002/24/10 02/24/10 11:09:02 11:09:56 1 6.8 11.0 652.8 208.7 43.502/24/10 02/24/10 11:10:00 11:10:57 1 6.7 11.0 654.3 208.9 43.802/24/10 02/24/10 11:11:00 11:11:58 1 6.7 11.0 656.0 208.5 47.902/24/10 02/24/10 11:12:01 11:12:59 1 6.7 11.0 653.5 208.9 45.302/24/10 02/24/10 11:13:02 11:13:57 1 6.8 10.9 651.1 208.8 44.102/24/10 02/24/10 11:14:00 11:14:57 1 6.8 10.9 649.6 208.6 43.202/24/10 02/24/10 11:15:00 11:15:58 1 6.9 10.9 648.3 208.5 40.102/24/10 02/24/10 11:16:01 11:16:59 1 6.9 10.8 646.5 207.1 36.902/24/10 02/24/10 11:17:02 11:17:57 1 6.9 10.8 645.9 206.4 39.602/24/10 02/24/10 11:18:00 11:18:58 1 6.8 10.9 649.1 206.4 41.602/24/10 02/24/10 11:19:01 11:19:58 1 6.7 11.0 652.2 206.2 37.302/24/10 02/24/10 11:20:01 11:20:59 1 6.8 11.0 650.3 206.1 36.402/24/10 02/24/10 11:21:02 11:21:57 1 6.8 10.9 648.7 206.4 38.4
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 11:22:00 11:22:58 1 6.8 10.9 648.6 207.0 41.702/24/10 02/24/10 11:23:01 11:23:58 1 6.9 10.8 645.2 206.8 43.102/24/10 02/24/10 11:24:01 11:24:59 1 6.9 10.9 647.1 206.5 44.202/24/10 02/24/10 11:25:02 11:25:57 1 6.9 10.9 646.0 206.5 45.702/24/10 02/24/10 11:26:00 11:26:58 1 6.8 10.9 647.7 206.5 41.202/24/10 02/24/10 11:27:01 11:27:59 1 6.8 10.9 647.4 206.5 38.702/24/10 02/24/10 11:28:02 11:28:59 1 6.8 11.0 651.2 206.9 35.902/24/10 02/24/10 11:29:02 11:29:57 1 6.8 11.0 649.9 207.6 37.102/24/10 02/24/10 11:30:00 11:30:58 1 6.9 10.9 647.0 207.9 40.502/24/10 02/24/10 11:31:01 11:31:59 1 6.9 10.9 646.7 208.0 41.402/24/10 02/24/10 11:32:02 11:32:57 1 6.9 10.8 645.1 208.3 41.602/24/10 02/24/10 11:33:00 11:33:57 1 7.0 10.8 642.7 208.0 40.002/24/10 02/24/10 11:34:00 11:34:58 1 7.0 10.8 642.5 208.0 39.102/24/10 02/24/10 11:35:01 11:35:59 1 6.9 10.9 646.0 208.1 36.102/24/10 02/24/10 11:36:02 11:36:57 1 6.8 10.9 647.0 208.5 36.302/24/10 02/24/10 11:37:00 11:37:57 1 6.8 10.9 648.2 208.5 37.002/24/10 02/24/10 11:38:00 11:38:58 1 6.8 10.9 648.7 208.4 37.202/24/10 02/24/10 11:39:01 11:39:59 1 6.8 10.9 647.3 208.3 38.602/24/10 02/24/10 11:40:02 11:40:57 1 6.8 10.9 646.4 207.9 37.102/24/10 02/24/10 11:41:00 11:41:58 1 7.0 10.8 641.4 208.0 39.202/24/10 02/24/10 11:42:01 11:42:59 1 7.0 10.8 640.3 208.1 35.702/24/10 02/24/10 11:43:02 11:43:57 1 6.9 10.8 641.5 208.0 34.802/24/10 02/24/10 11:44:00 11:44:57 1 6.9 10.9 642.9 208.4 41.602/24/10 02/24/10 11:45:00 11:45:58 1 6.9 10.9 644.8 208.5 35.702/24/10 02/24/10 11:46:01 11:46:59 1 6.8 11.0 647.4 208.5 38.902/24/10 02/24/10 11:47:02 11:47:57 1 6.8 11.0 648.0 208.5 35.802/24/10 02/24/10 11:48:00 11:48:58 1 6.8 11.0 647.1 208.1 35.702/24/10 02/24/10 11:49:01 11:49:58 1 6.9 10.9 644.4 208.4 34.302/24/10 02/24/10 11:50:01 11:50:57 1 6.9 10.9 642.1 208.5 35.902/24/10 02/24/10 11:51:00 11:51:57 1 6.9 10.9 644.1 208.5 38.502/24/10 02/24/10 11:52:00 11:52:58 1 6.9 10.8 642.3 208.2 37.902/24/10 02/24/10 11:53:01 11:53:59 1 6.9 10.9 642.9 208.4 36.802/24/10 02/24/10 11:54:02 11:54:57 1 6.9 10.9 645.4 208.6 36.402/24/10 02/24/10 11:55:00 11:55:58 1 6.7 11.0 655.7 208.5 36.102/24/10 02/24/10 11:56:01 11:56:58 1 7.0 11.3 646.1 207.2 38.102/24/10 02/24/10 11:57:01 11:57:59 1 7.3 11.4 627.3 201.3 39.902/24/10 02/24/10 11:58:02 11:58:57 1 7.4 11.4 625.1 198.4 42.5
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 11:59:00 11:59:58 1 7.4 11.4 621.6 198.0 41.9

Average 6.9 10.9 639.1 204.7 37.3

Minimum Value

Maximum Value

6.7 10.8 612.6 198.0 11.87.4 11.4 656.0 208.9 60.1
Vienna

Emission Report

NRG

Unit: 8

Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 13:15:02 13:15:57 2 6.8 11.2 682.5 208.2 1.902/24/10 02/24/10 13:16:00 13:16:58 2 6.8 11.2 683.9 208.1 5.702/24/10 02/24/10 13:17:01 13:17:59 2 6.8 11.2 684.3 208.2 8.002/24/10 02/24/10 13:18:02 13:18:59 2 6.8 11.2 685.5 208.0 5.602/24/10 02/24/10 13:19:03 13:19:57 2 6.8 11.2 684.4 208.5 4.702/24/10 02/24/10 13:20:00 13:20:58 2 6.8 11.2 685.1 208.5 5.602/24/10 02/24/10 13:21:01 13:21:59 2 6.8 11.2 683.0 208.4 6.302/24/10 02/24/10 13:22:02 13:22:57 2 6.8 11.2 682.6 208.0 2.502/24/10 02/24/10 13:23:00 13:23:58 2 6.8 11.2 682.2 208.0 5.402/24/10 02/24/10 13:24:01 13:24:58 2 6.8 11.2 683.1 208.0 4.102/24/10 02/24/10 13:25:01 13:25:59 2 6.8 11.2 683.5 207.8 7.402/24/10 02/24/10 13:26:02 13:26:57 2 6.8 11.2 683.3 207.6 7.302/24/10 02/24/10 13:27:00 13:27:58 2 6.8 11.2 684.5 208.1 4.602/24/10 02/24/10 13:28:01 13:28:59 2 6.8 11.2 682.0 207.9 3.702/24/10 02/24/10 13:29:02 13:29:57 2 6.8 11.1 682.8 207.5 4.302/24/10 02/24/10 13:30:00 13:30:58 2 6.8 11.1 682.7 207.8 6.502/24/10 02/24/10 13:31:01 13:31:59 2 6.9 11.1 679.6 208.1 5.002/24/10 02/24/10 13:32:02 13:32:57 2 6.9 11.1 680.4 208.1 5.402/24/10 02/24/10 13:33:00 13:33:58 2 6.8 11.1 682.6 208.2 4.102/24/10 02/24/10 13:34:01 13:34:59 2 6.8 11.2 683.7 208.1 1.802/24/10 02/24/10 13:35:02 13:35:59 2 6.8 11.2 684.7 208.1 3.302/24/10 02/24/10 13:36:02 13:36:57 2 6.8 11.2 684.1 208.1 1.302/24/10 02/24/10 13:37:00 13:37:58 2 6.8 11.1 682.6 208.1 3.202/24/10 02/24/10 13:38:01 13:38:59 2 6.9 11.1 682.3 208.1 3.702/24/10 02/24/10 13:39:02 13:39:57 2 6.9 11.1 682.9 208.7 0.502/24/10 02/24/10 13:40:00 13:40:57 2 6.9 11.1 681.5 208.2 0.902/24/10 02/24/10 13:41:00 13:41:58 2 6.8 11.1 684.9 207.6 1.502/24/10 02/24/10 13:42:01 13:42:59 2 6.8 11.1 685.4 208.4 5.002/24/10 02/24/10 13:43:02 13:43:57 2 6.8 11.1 684.2 208.6 5.002/24/10 02/24/10 13:44:00 13:44:58 2 6.8 11.1 685.7 208.3 3.702/24/10 02/24/10 13:45:01 13:45:59 2 6.8 11.1 684.2 208.6 3.8
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 13:46:02 13:46:57 2 6.8 11.1 685.4 208.8 4.202/24/10 02/24/10 13:47:00 13:47:58 2 6.8 11.0 682.7 208.3 4.202/24/10 02/24/10 13:48:01 13:48:59 2 6.9 11.0 680.7 208.6 2.602/24/10 02/24/10 13:49:02 13:49:59 2 6.9 11.0 679.4 208.5 3.502/24/10 02/24/10 13:50:02 13:50:57 2 6.9 11.0 678.3 208.4 1.502/24/10 02/24/10 13:51:00 13:51:58 2 6.9 11.0 678.4 208.5 3.802/24/10 02/24/10 13:52:01 13:52:59 2 6.9 11.0 678.3 208.0 1.902/24/10 02/24/10 13:53:02 13:53:57 2 6.8 11.1 679.4 208.2 -0.702/24/10 02/24/10 13:54:00 13:54:58 2 6.9 11.0 677.4 208.5 3.802/24/10 02/24/10 13:55:01 13:55:59 2 6.9 11.0 675.1 208.7 1.702/24/10 02/24/10 13:56:02 13:56:57 2 7.0 11.0 672.1 209.0 2.902/24/10 02/24/10 13:57:00 13:57:57 2 7.0 11.0 671.6 208.7 -0.602/24/10 02/24/10 13:58:00 13:58:58 2 7.0 11.0 670.9 209.0 11.002/24/10 02/24/10 13:59:01 13:59:59 2 7.0 10.9 669.7 208.7 10.602/24/10 02/24/10 14:00:02 14:00:58 2 7.0 11.0 670.5 208.6 9.802/24/10 02/24/10 14:01:01 14:01:59 2 7.0 11.0 670.9 208.6 9.302/24/10 02/24/10 14:02:02 14:02:57 2 6.9 11.0 674.3 209.3 9.502/24/10 02/24/10 14:03:00 14:03:58 2 6.9 11.0 671.7 209.6 8.102/24/10 02/24/10 14:04:01 14:04:59 2 7.0 11.0 668.9 208.3 7.402/24/10 02/24/10 14:05:02 14:05:59 2 7.0 10.9 666.7 208.2 7.202/24/10 02/24/10 14:06:03 14:06:57 2 7.0 10.9 665.0 208.7 2.902/24/10 02/24/10 14:07:00 14:07:58 2 7.0 11.0 667.4 208.8 7.002/24/10 02/24/10 14:08:01 14:08:59 2 7.0 10.9 666.0 208.1 5.302/24/10 02/24/10 14:09:02 14:09:57 2 7.0 11.0 666.4 207.9 5.502/24/10 02/24/10 14:10:00 14:10:58 2 7.0 11.0 666.8 208.7 5.402/24/10 02/24/10 14:11:01 14:11:59 2 7.0 11.0 666.4 208.6 -0.402/24/10 02/24/10 14:12:02 14:12:59 2 7.0 10.9 664.7 207.9 3.602/24/10 02/24/10 14:13:02 14:13:57 2 7.0 11.0 666.7 208.0 11.302/24/10 02/24/10 14:14:00 14:14:58 2 7.0 11.0 666.4 208.2 11.102/24/10 02/24/10 14:15:01 14:15:59 2 7.0 11.0 663.9 208.0 4.902/24/10 02/24/10 14:16:02 14:16:59 2 7.0 10.9 661.8 208.5 8.602/24/10 02/24/10 14:17:03 14:17:57 2 7.0 10.9 663.4 208.5 10.502/24/10 02/24/10 14:18:00 14:18:58 2 7.0 11.0 664.4 208.2 11.402/24/10 02/24/10 14:19:01 14:19:59 2 6.9 11.0 667.3 208.1 13.502/24/10 02/24/10 14:20:02 14:20:57 2 7.0 11.0 665.7 208.4 11.602/24/10 02/24/10 14:21:00 14:21:57 2 6.9 11.0 667.9 208.3 10.902/24/10 02/24/10 14:22:00 14:22:58 2 7.0 10.9 664.0 208.2 9.6
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 14:23:01 14:23:59 2 7.0 10.9 663.2 208.8 12.902/24/10 02/24/10 14:24:02 14:24:57 2 7.0 10.9 664.8 208.5 11.202/24/10 02/24/10 14:25:00 14:25:58 2 7.0 11.0 664.9 208.1 16.402/24/10 02/24/10 14:26:01 14:26:58 2 7.0 11.0 665.4 208.4 15.302/24/10 02/24/10 14:27:01 14:27:59 2 7.0 11.0 665.4 209.0 16.202/24/10 02/24/10 14:28:02 14:28:57 2 7.0 11.0 665.7 209.0 14.702/24/10 02/24/10 14:29:00 14:29:58 2 7.0 11.0 666.3 208.6 10.602/24/10 02/24/10 14:30:01 14:30:59 2 7.0 11.0 666.7 208.7 16.802/24/10 02/24/10 14:31:02 14:31:57 2 7.0 11.0 667.2 208.7 13.102/24/10 02/24/10 14:32:00 14:32:57 2 7.0 10.9 663.7 209.0 11.202/24/10 02/24/10 14:33:00 14:33:58 2 7.0 10.9 664.6 208.5 3.802/24/10 02/24/10 14:34:01 14:34:59 2 7.0 10.9 666.2 208.6 5.202/24/10 02/24/10 14:35:02 14:35:57 2 7.0 10.9 665.1 209.0 7.502/24/10 02/24/10 14:36:00 14:36:58 2 7.0 11.0 668.5 209.2 11.702/24/10 02/24/10 14:37:01 14:37:59 2 6.9 11.0 669.2 208.9 12.402/24/10 02/24/10 14:38:02 14:38:56 2 7.0 11.0 668.8 208.8 11.202/24/10 02/24/10 14:39:00 14:39:57 2 7.0 11.0 669.5 208.9 10.202/24/10 02/24/10 14:40:00 14:40:58 2 7.0 10.9 668.1 209.0 8.602/24/10 02/24/10 14:41:01 14:41:59 2 7.0 10.9 666.0 209.5 13.502/24/10 02/24/10 14:42:02 14:42:57 2 7.1 10.9 662.5 209.7 14.702/24/10 02/24/10 14:43:00 14:43:58 2 7.0 10.9 664.9 209.5 10.102/24/10 02/24/10 14:44:01 14:44:59 2 7.0 11.0 668.6 209.5 11.702/24/10 02/24/10 14:45:02 14:45:59 2 7.0 11.0 666.9 209.0 7.802/24/10 02/24/10 14:46:02 14:46:57 2 7.0 11.0 667.9 209.3 4.002/24/10 02/24/10 14:47:00 14:47:58 2 6.9 11.0 670.5 209.3 3.402/24/10 02/24/10 14:48:01 14:48:59 2 6.9 11.0 670.4 209.1 5.602/24/10 02/24/10 14:49:02 14:49:57 2 6.9 11.0 670.8 209.1 3.302/24/10 02/24/10 14:50:00 14:50:57 2 7.0 11.0 668.1 209.1 6.902/24/10 02/24/10 14:51:01 14:51:58 2 7.0 11.0 665.4 209.1 8.002/24/10 02/24/10 14:52:01 14:52:59 2 7.0 11.0 665.5 208.9 8.602/24/10 02/24/10 14:53:02 14:53:57 2 7.0 11.0 664.1 208.8 7.402/24/10 02/24/10 14:54:00 14:54:58 2 7.0 11.0 665.8 209.2 5.702/24/10 02/24/10 14:55:01 14:55:59 2 6.9 11.1 669.5 209.5 6.302/24/10 02/24/10 14:56:02 14:56:59 2 6.9 11.1 671.2 209.3 7.202/24/10 02/24/10 14:57:03 14:57:57 2 6.9 11.0 668.3 209.0 7.602/24/10 02/24/10 14:58:00 14:58:58 2 6.9 11.0 667.8 208.5 12.302/24/10 02/24/10 14:59:01 14:59:59 2 7.0 11.0 665.7 208.9 17.5
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 15:00:02 15:00:57 2 7.0 10.9 663.3 208.9 11.502/24/10 02/24/10 15:01:00 15:01:58 2 7.0 11.0 666.4 209.0 13.402/24/10 02/24/10 15:02:01 15:02:58 2 7.0 11.0 668.6 209.4 12.302/24/10 02/24/10 15:03:01 15:03:59 2 6.9 11.0 670.2 209.5 10.102/24/10 02/24/10 15:04:02 15:04:57 2 6.9 11.0 667.8 209.5 9.402/24/10 02/24/10 15:05:00 15:05:58 2 6.9 11.0 667.3 209.5 11.002/24/10 02/24/10 15:06:01 15:06:59 2 7.0 11.0 666.8 209.5 5.502/24/10 02/24/10 15:07:02 15:07:59 2 6.9 11.0 668.1 209.8 4.402/24/10 02/24/10 15:08:02 15:08:57 2 7.0 10.9 663.2 209.9 5.602/24/10 02/24/10 15:09:00 15:09:58 2 7.0 10.9 661.7 209.1 3.402/24/10 02/24/10 15:10:01 15:10:59 2 7.1 10.9 661.0 209.0 5.802/24/10 02/24/10 15:11:02 15:11:57 2 7.1 10.8 657.7 209.1 6.402/24/10 02/24/10 15:12:00 15:12:58 2 7.1 10.9 660.7 209.1 10.802/24/10 02/24/10 15:13:01 15:13:59 2 7.0 10.9 662.9 209.5 11.702/24/10 02/24/10 15:14:02 15:14:59 2 7.0 10.9 662.8 209.1 12.302/24/10 02/24/10 15:15:03 15:15:57 2 7.1 10.9 661.8 208.8 9.102/24/10 02/24/10 15:16:00 15:16:58 2 7.0 10.9 661.9 208.5 9.802/24/10 02/24/10 15:17:01 15:17:59 2 7.1 10.9 660.9 209.2 6.402/24/10 02/24/10 15:18:02 15:18:57 2 7.1 10.8 660.5 209.0 4.802/24/10 02/24/10 15:19:00 15:19:58 2 7.1 10.8 658.0 209.0 6.002/24/10 02/24/10 15:20:01 15:20:59 2 7.2 10.8 657.1 208.9 3.002/24/10 02/24/10 15:21:02 15:21:59 2 7.2 10.8 657.4 208.8 5.602/24/10 02/24/10 15:22:02 15:22:57 2 7.1 10.8 658.0 208.9 0.502/24/10 02/24/10 15:23:00 15:23:58 2 7.1 10.9 660.3 208.8 11.002/24/10 02/24/10 15:24:01 15:24:59 2 7.0 11.0 664.1 209.4 11.802/24/10 02/24/10 15:25:02 15:25:57 2 7.0 11.0 662.8 209.4 13.802/24/10 02/24/10 15:26:00 15:26:58 2 7.0 11.0 661.6 209.0 4.502/24/10 02/24/10 15:27:01 15:27:59 2 7.1 10.9 659.8 209.8 6.902/24/10 02/24/10 15:28:02 15:28:59 2 7.1 10.9 658.0 208.7 5.102/24/10 02/24/10 15:29:02 15:29:57 2 7.1 10.9 657.2 209.2 7.502/24/10 02/24/10 15:30:00 15:30:58 2 7.2 10.8 656.4 209.0 8.302/24/10 02/24/10 15:31:01 15:31:59 2 7.1 10.9 660.6 208.7 12.402/24/10 02/24/10 15:32:02 15:32:57 2 7.0 10.9 662.1 208.9 10.902/24/10 02/24/10 15:33:00 15:33:58 2 7.0 11.0 661.7 209.0 9.302/24/10 02/24/10 15:34:01 15:34:59 2 7.0 10.9 657.9 207.7 9.302/24/10 02/24/10 15:35:02 15:35:56 2 6.6 10.3 625.1 197.4 8.602/24/10 02/24/10 15:36:00 15:36:57 2 6.6 10.3 621.7 196.1 9.9
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 15:37:00 15:37:58 2 6.6 10.3 621.5 196.3 8.202/24/10 02/24/10 15:38:01 15:38:59 2 6.7 10.4 625.1 197.1 12.202/24/10 02/24/10 15:39:02 15:39:57 2 7.0 10.9 645.9 202.9 10.502/24/10 02/24/10 15:40:00 15:40:58 2 7.5 11.3 635.3 199.6 10.802/24/10 02/24/10 15:41:01 15:41:58 2 7.4 11.2 640.8 200.0 9.302/24/10 02/24/10 15:42:01 15:42:59 2 6.9 10.9 660.5 207.7 7.002/24/10 02/24/10 15:43:02 15:43:57 2 6.6 10.6 640.6 202.6 10.202/24/10 02/24/10 15:44:00 15:44:58 2 6.6 10.5 637.0 200.0 5.802/24/10 02/24/10 15:45:01 15:45:59 2 6.6 10.6 640.2 199.5 3.302/24/10 02/24/10 15:46:02 15:46:57 2 6.7 10.7 647.8 202.4 -0.602/24/10 02/24/10 15:47:00 15:47:58 2 6.6 10.5 636.0 201.0 -4.002/24/10 02/24/10 15:48:01 15:48:58 2 6.7 10.6 641.2 200.3 1.702/24/10 02/24/10 15:49:01 15:49:59 2 7.0 11.0 660.8 204.6 7.902/24/10 02/24/10 15:50:02 15:50:57 2 7.0 11.0 662.5 208.1 8.802/24/10 02/24/10 15:51:00 15:51:58 2 7.0 11.0 664.1 208.4 2.002/24/10 02/24/10 15:52:01 15:52:59 2 6.9 11.0 667.7 208.5 11.502/24/10 02/24/10 15:53:02 15:53:57 2 6.8 11.1 670.4 208.4 9.302/24/10 02/24/10 15:54:00 15:54:57 2 6.8 11.1 669.3 209.0 6.602/24/10 02/24/10 15:55:00 15:55:58 2 6.8 11.0 669.6 208.4 6.402/24/10 02/24/10 15:56:01 15:56:59 2 6.9 11.0 668.1 208.3 8.102/24/10 02/24/10 15:57:02 15:57:57 2 6.9 11.0 667.1 208.1 6.902/24/10 02/24/10 15:58:00 15:58:58 2 6.9 11.0 666.3 208.7 4.602/24/10 02/24/10 15:59:01 15:59:58 2 6.9 11.0 667.5 208.7 6.802/24/10 02/24/10 16:00:01 16:00:59 2 7.0 11.0 663.0 208.6 11.302/24/10 02/24/10 16:01:02 16:01:57 2 7.0 11.0 665.1 208.9 11.602/24/10 02/24/10 16:02:00 16:02:58 2 6.9 11.0 665.8 208.7 12.302/24/10 02/24/10 16:03:01 16:03:59 2 6.9 11.0 668.0 208.1 9.202/24/10 02/24/10 16:04:02 16:04:56 2 6.8 11.1 670.3 208.2 9.602/24/10 02/24/10 16:05:00 16:05:57 2 6.8 11.1 669.5 208.6 9.602/24/10 02/24/10 16:06:00 16:06:58 2 6.8 11.1 670.5 209.4 5.102/24/10 02/24/10 16:07:01 16:07:59 2 6.9 11.0 666.8 208.7 8.002/24/10 02/24/10 16:08:02 16:08:57 2 6.9 11.0 666.0 208.7 9.602/24/10 02/24/10 16:09:00 16:09:58 2 7.0 11.0 665.0 209.3 5.602/24/10 02/24/10 16:10:01 16:10:59 2 7.0 11.0 662.8 209.0 11.702/24/10 02/24/10 16:11:02 16:11:59 2 7.0 11.0 663.6 209.0 12.002/24/10 02/24/10 16:12:02 16:12:57 2 6.9 11.0 666.1 209.0 14.902/24/10 02/24/10 16:13:00 16:13:58 2 6.9 11.0 667.6 208.6 13.8
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 16:14:01 16:14:59 2 6.9 11.0 666.7 208.8 9.9

Average 6.9 11.0 667.1 208.0 7.5

Minimum Value

Maximum Value

6.6 10.3 621.5 196.1 -4.07.5 11.3 685.7 209.9 17.5
Vienna

Emission Report

NRG

Unit: 8

Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 16:35:03 16:35:58 3 6.8 11.1 666.1 208.4 3.802/24/10 02/24/10 16:36:01 16:36:59 3 6.8 11.2 670.1 208.5 3.702/24/10 02/24/10 16:37:02 16:37:57 3 6.9 11.1 668.1 208.4 4.102/24/10 02/24/10 16:38:00 16:38:58 3 7.0 11.0 665.2 208.0 -1.502/24/10 02/24/10 16:39:01 16:39:59 3 7.0 11.0 665.3 208.2 0.702/24/10 02/24/10 16:40:02 16:40:57 3 7.0 11.0 665.9 208.6 5.902/24/10 02/24/10 16:41:00 16:41:58 3 7.0 11.0 666.5 208.7 8.702/24/10 02/24/10 16:42:01 16:42:59 3 7.0 11.0 667.9 208.6 7.702/24/10 02/24/10 16:43:02 16:43:57 3 7.0 11.0 667.6 208.4 6.402/24/10 02/24/10 16:44:00 16:44:58 3 6.9 11.1 673.5 208.6 6.702/24/10 02/24/10 16:45:01 16:45:59 3 6.8 11.2 675.8 209.0 6.902/24/10 02/24/10 16:46:02 16:46:57 3 6.8 11.2 674.9 208.6 5.502/24/10 02/24/10 16:47:00 16:47:58 3 6.8 11.2 675.5 208.8 4.202/24/10 02/24/10 16:48:01 16:48:59 3 6.9 11.1 673.2 209.2 3.802/24/10 02/24/10 16:49:02 16:49:57 3 6.9 11.1 672.8 208.5 3.602/24/10 02/24/10 16:50:00 16:50:58 3 6.9 11.1 672.0 208.2 6.402/24/10 02/24/10 16:51:01 16:51:59 3 6.9 11.1 672.6 208.1 3.902/24/10 02/24/10 16:52:03 16:52:58 3 6.9 11.2 673.3 208.5 5.902/24/10 02/24/10 16:53:01 16:53:59 3 6.8 11.2 676.6 208.5 1.902/24/10 02/24/10 16:54:02 16:54:57 3 6.8 11.1 676.9 208.5 1.202/24/10 02/24/10 16:55:00 16:55:58 3 6.8 11.2 677.3 208.5 5.202/24/10 02/24/10 16:56:01 16:56:59 3 6.8 11.2 679.1 208.8 2.202/24/10 02/24/10 16:57:02 16:57:57 3 6.8 11.2 678.3 208.6 -3.302/24/10 02/24/10 16:58:00 16:58:59 3 6.8 11.1 675.0 207.9 3.202/24/10 02/24/10 16:59:02 16:59:57 3 6.8 11.1 675.6 208.0 3.002/24/10 02/24/10 17:00:00 17:00:58 3 6.8 11.1 674.5 208.0 4.402/24/10 02/24/10 17:01:01 17:01:59 3 6.9 11.0 670.3 208.2 4.602/24/10 02/24/10 17:02:03 17:02:58 3 6.9 11.0 670.2 208.1 -4.302/24/10 02/24/10 17:03:01 17:03:59 3 6.9 11.0 669.0 208.2 1.502/24/10 02/24/10 17:04:02 17:04:57 3 6.9 11.0 669.4 208.1 6.502/24/10 02/24/10 17:05:00 17:05:58 3 6.9 11.1 671.8 208.0 5.6
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 17:06:01 17:06:59 3 6.9 11.1 671.1 208.1 6.902/24/10 02/24/10 17:07:02 17:07:58 3 6.8 11.1 672.8 208.4 8.302/24/10 02/24/10 17:08:01 17:08:59 3 6.8 11.1 673.1 208.9 5.602/24/10 02/24/10 17:09:02 17:09:57 3 6.9 11.1 669.4 208.0 2.902/24/10 02/24/10 17:10:00 17:10:58 3 6.9 11.1 670.0 208.1 3.602/24/10 02/24/10 17:11:02 17:11:57 3 6.9 11.0 668.5 208.6 6.202/24/10 02/24/10 17:12:00 17:12:58 3 7.0 11.0 666.7 208.5 10.102/24/10 02/24/10 17:13:01 17:13:59 3 7.0 11.1 667.4 208.8 0.402/24/10 02/24/10 17:14:02 17:14:57 3 7.0 11.0 666.5 208.3 4.202/24/10 02/24/10 17:15:00 17:15:58 3 6.9 11.1 669.6 208.1 4.902/24/10 02/24/10 17:16:01 17:16:57 3 6.9 11.1 670.2 208.3 7.202/24/10 02/24/10 17:17:00 17:17:58 3 6.9 11.1 669.7 208.1 1.802/24/10 02/24/10 17:18:01 17:18:59 3 6.9 11.1 671.8 208.1 -5.302/24/10 02/24/10 17:19:02 17:19:57 3 6.9 11.1 669.2 208.0 -9.202/24/10 02/24/10 17:20:00 17:20:59 3 7.0 11.0 667.7 208.0 5.002/24/10 02/24/10 17:21:02 17:21:57 3 7.0 11.0 664.0 208.0 5.202/24/10 02/24/10 17:22:00 17:22:58 3 7.1 11.0 662.5 208.4 5.902/24/10 02/24/10 17:23:01 17:23:59 3 7.0 11.0 663.0 208.8 7.802/24/10 02/24/10 17:24:02 17:24:57 3 7.0 11.0 665.7 208.8 8.702/24/10 02/24/10 17:25:00 17:25:59 3 7.0 11.0 668.0 208.6 9.002/24/10 02/24/10 17:26:02 17:26:57 3 6.9 11.0 670.2 208.8 8.302/24/10 02/24/10 17:27:00 17:27:58 3 6.9 11.0 670.3 208.9 9.102/24/10 02/24/10 17:28:01 17:28:59 3 7.0 11.0 665.5 208.6 20.502/24/10 02/24/10 17:29:02 17:29:57 3 7.0 11.0 665.6 209.0 12.602/24/10 02/24/10 17:30:00 17:30:59 3 7.0 11.0 666.4 209.0 22.402/24/10 02/24/10 17:31:02 17:31:57 3 7.0 11.0 665.9 208.5 23.502/24/10 02/24/10 17:32:00 17:32:58 3 6.9 11.1 668.6 208.5 23.102/24/10 02/24/10 17:33:01 17:33:59 3 6.9 11.1 670.5 208.5 20.802/24/10 02/24/10 17:34:03 17:34:58 3 6.8 11.1 673.5 208.4 22.802/24/10 02/24/10 17:35:01 17:35:59 3 6.8 11.1 672.7 208.6 26.702/24/10 02/24/10 17:36:02 17:36:57 3 6.8 11.1 671.6 208.7 19.202/24/10 02/24/10 17:37:00 17:37:58 3 6.9 11.1 669.2 209.2 13.102/24/10 02/24/10 17:38:01 17:38:59 3 7.0 11.0 666.5 209.1 20.002/24/10 02/24/10 17:39:02 17:39:58 3 6.9 11.0 667.6 208.9 19.502/24/10 02/24/10 17:40:01 17:40:59 3 6.9 11.1 667.8 208.7 17.002/24/10 02/24/10 17:41:02 17:41:57 3 6.9 11.0 668.0 207.8 13.702/24/10 02/24/10 17:42:00 17:42:58 3 6.8 11.2 673.0 207.9 18.9
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 17:43:01 17:43:59 3 6.8 11.2 671.5 208.0 17.102/24/10 02/24/10 17:44:02 17:44:57 3 6.8 11.2 674.1 207.6 19.102/24/10 02/24/10 17:45:01 17:45:59 3 6.8 11.1 671.3 206.0 25.602/24/10 02/24/10 17:46:02 17:46:57 3 7.0 11.1 666.5 198.1 23.302/24/10 02/24/10 17:47:00 17:47:58 3 7.0 11.1 664.9 196.2 20.302/24/10 02/24/10 17:48:01 17:48:59 3 7.0 11.0 662.2 196.2 12.002/24/10 02/24/10 17:49:02 17:49:57 3 7.1 11.0 660.0 196.3 16.502/24/10 02/24/10 17:50:00 17:50:58 3 7.0 11.0 657.1 196.5 17.302/24/10 02/24/10 17:51:01 17:51:57 3 7.0 11.1 663.1 196.1 22.902/24/10 02/24/10 17:52:00 17:52:58 3 7.0 11.1 664.3 196.2 20.202/24/10 02/24/10 17:53:01 17:53:59 3 7.0 11.1 665.3 196.5 21.002/24/10 02/24/10 17:54:02 17:54:57 3 7.0 11.0 663.8 196.4 9.802/24/10 02/24/10 17:55:00 17:55:58 3 7.1 11.0 659.8 196.5 19.302/24/10 02/24/10 17:56:02 17:56:57 3 7.1 11.0 658.5 196.6 20.902/24/10 02/24/10 17:57:00 17:57:58 3 7.1 10.9 656.6 196.8 20.302/24/10 02/24/10 17:58:01 17:58:59 3 7.1 11.0 660.9 196.2 19.602/24/10 02/24/10 17:59:02 17:59:57 3 7.0 11.0 660.5 196.3 20.302/24/10 02/24/10 18:00:00 18:00:58 3 7.0 11.0 662.6 196.9 22.402/24/10 02/24/10 18:01:02 18:01:57 3 7.0 11.0 664.5 197.0 22.702/24/10 02/24/10 18:02:00 18:02:58 3 7.0 11.0 664.7 197.0 20.002/24/10 02/24/10 18:03:01 18:03:59 3 7.0 11.0 663.9 196.8 22.702/24/10 02/24/10 18:04:02 18:04:57 3 7.0 11.0 663.7 196.4 14.202/24/10 02/24/10 18:05:00 18:05:59 3 7.0 11.0 663.3 196.5 18.402/24/10 02/24/10 18:06:02 18:06:57 3 6.9 11.0 666.2 196.6 18.202/24/10 02/24/10 18:07:00 18:07:58 3 7.0 11.0 665.4 196.8 15.002/24/10 02/24/10 18:08:01 18:08:59 3 6.8 11.1 669.0 196.5 7.302/24/10 02/24/10 18:09:02 18:09:57 3 6.9 11.1 668.3 196.4 10.902/24/10 02/24/10 18:10:00 18:10:59 3 6.9 11.1 668.0 196.5 15.402/24/10 02/24/10 18:11:02 18:11:57 3 6.9 11.1 666.1 196.9 15.202/24/10 02/24/10 18:12:00 18:12:58 3 7.0 11.0 661.9 196.8 9.002/24/10 02/24/10 18:13:01 18:13:59 3 7.0 11.0 661.9 196.9 14.202/24/10 02/24/10 18:14:02 18:14:57 3 7.0 11.0 662.1 196.6 15.802/24/10 02/24/10 18:15:00 18:15:58 3 7.0 11.1 663.6 196.3 16.302/24/10 02/24/10 18:16:01 18:16:57 3 7.0 11.1 663.6 195.7 16.902/24/10 02/24/10 18:17:00 18:17:58 3 7.0 11.1 663.9 196.2 15.402/24/10 02/24/10 18:18:01 18:18:59 3 7.0 11.1 664.4 196.8 20.002/24/10 02/24/10 18:19:02 18:19:57 3 6.9 11.1 666.4 196.8 9.1
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 18:20:00 18:20:59 3 6.9 11.1 664.9 196.8 16.202/24/10 02/24/10 18:21:02 18:21:57 3 7.0 11.1 663.3 196.7 16.102/24/10 02/24/10 18:22:00 18:22:58 3 7.0 11.0 661.5 196.0 17.602/24/10 02/24/10 18:23:01 18:23:59 3 7.0 11.0 661.0 195.9 12.702/24/10 02/24/10 18:24:02 18:24:58 3 7.1 11.0 659.3 195.9 7.102/24/10 02/24/10 18:25:01 18:25:59 3 7.0 11.1 661.9 196.0 11.102/24/10 02/24/10 18:26:02 18:26:57 3 7.0 11.1 662.7 196.1 16.502/24/10 02/24/10 18:27:00 18:27:58 3 7.0 11.1 662.5 196.0 9.602/24/10 02/24/10 18:28:01 18:28:59 3 6.9 11.2 666.9 196.0 9.802/24/10 02/24/10 18:29:02 18:29:57 3 6.9 11.2 668.1 195.4 10.802/24/10 02/24/10 18:30:00 18:30:59 3 6.8 11.2 671.2 195.6 9.502/24/10 02/24/10 18:31:02 18:31:57 3 6.9 11.2 666.1 195.9 12.102/24/10 02/24/10 18:32:00 18:32:58 3 7.0 11.2 664.0 195.5 15.702/24/10 02/24/10 18:33:01 18:33:59 3 7.0 11.1 662.2 195.5 12.502/24/10 02/24/10 18:34:02 18:34:57 3 7.0 11.1 660.4 195.4 10.802/24/10 02/24/10 18:35:01 18:35:59 3 7.0 11.1 663.3 195.3 17.002/24/10 02/24/10 18:36:02 18:36:57 3 6.9 11.1 665.6 195.5 11.802/24/10 02/24/10 18:37:00 18:37:58 3 6.9 11.2 667.0 195.5 15.702/24/10 02/24/10 18:38:01 18:38:59 3 6.9 11.2 667.2 195.5 11.602/24/10 02/24/10 18:39:02 18:39:58 3 6.8 11.2 667.5 195.8 15.702/24/10 02/24/10 18:40:01 18:40:59 3 7.5 11.5 635.2 186.0 17.102/24/10 02/24/10 18:41:02 18:41:57 3 8.0 11.9 608.8 180.2 18.202/24/10 02/24/10 18:42:00 18:42:58 3 8.2 12.0 600.2 176.0 20.602/24/10 02/24/10 18:43:01 18:43:59 3 8.1 12.0 603.4 175.6 9.302/24/10 02/24/10 18:44:02 18:44:57 3 7.3 11.3 631.6 184.7 11.902/24/10 02/24/10 18:45:00 18:45:59 3 6.4 10.4 619.1 182.3 15.802/24/10 02/24/10 18:46:02 18:46:57 3 6.5 10.9 639.2 187.7 9.502/24/10 02/24/10 18:47:00 18:47:58 3 6.5 10.6 634.4 187.4 16.102/24/10 02/24/10 18:48:01 18:48:59 3 6.4 10.4 621.1 184.1 16.002/24/10 02/24/10 18:49:02 18:49:57 3 6.5 10.7 631.9 185.8 15.602/24/10 02/24/10 18:50:00 18:50:59 3 6.4 10.4 628.1 184.6 16.302/24/10 02/24/10 18:51:02 18:51:57 3 6.3 10.5 624.1 183.7 14.902/24/10 02/24/10 18:52:00 18:52:58 3 6.3 10.5 626.0 183.1 17.102/24/10 02/24/10 18:53:01 18:53:59 3 6.4 10.4 623.8 183.1 11.402/24/10 02/24/10 18:54:02 18:54:57 3 6.5 10.7 633.5 186.6 23.502/24/10 02/24/10 18:55:00 18:55:58 3 6.9 11.1 665.1 195.7 18.702/24/10 02/24/10 18:56:01 18:56:57 3 6.9 11.1 668.5 196.3 21.8
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 18:57:00 18:57:58 3 6.9 11.1 667.7 196.4 19.802/24/10 02/24/10 18:58:01 18:58:59 3 6.8 11.2 672.9 196.1 19.802/24/10 02/24/10 18:59:02 18:59:57 3 6.8 11.2 674.2 196.1 17.202/24/10 02/24/10 19:00:00 19:00:59 3 6.8 11.2 672.2 196.1 23.202/24/10 02/24/10 19:01:02 19:01:57 3 6.8 11.1 672.4 196.1 22.702/24/10 02/24/10 19:02:00 19:02:58 3 6.8 11.1 671.3 196.1 21.402/24/10 02/24/10 19:03:01 19:03:59 3 6.9 11.0 668.4 195.8 15.902/24/10 02/24/10 19:04:02 19:04:57 3 7.0 11.0 667.2 196.1 19.202/24/10 02/24/10 19:05:00 19:05:59 3 6.9 11.0 668.4 196.3 19.602/24/10 02/24/10 19:06:02 19:06:57 3 6.9 11.1 667.3 196.0 18.602/24/10 02/24/10 19:07:00 19:07:58 3 6.9 11.1 663.4 195.1 19.102/24/10 02/24/10 19:08:01 19:08:59 3 6.8 11.2 670.1 194.7 19.002/24/10 02/24/10 19:09:02 19:09:57 3 6.9 11.1 668.9 195.2 22.602/24/10 02/24/10 19:10:00 19:10:59 3 6.9 11.1 666.4 195.2 19.202/24/10 02/24/10 19:11:02 19:11:57 3 6.9 11.0 666.3 195.0 21.202/24/10 02/24/10 19:12:00 19:12:58 3 7.0 11.0 664.7 194.8 21.302/24/10 02/24/10 19:13:01 19:13:59 3 7.0 11.0 663.8 194.5 27.402/24/10 02/24/10 19:14:02 19:14:57 3 7.0 11.1 667.4 194.3 20.702/24/10 02/24/10 19:15:00 19:15:59 3 6.9 11.1 669.5 194.3 25.502/24/10 02/24/10 19:16:02 19:16:57 3 6.9 11.1 670.1 194.3 21.902/24/10 02/24/10 19:17:00 19:17:58 3 6.9 11.1 671.5 194.6 21.802/24/10 02/24/10 19:18:01 19:18:59 3 6.9 11.1 668.0 194.5 19.402/24/10 02/24/10 19:19:02 19:19:57 3 7.0 11.1 665.1 194.2 16.602/24/10 02/24/10 19:20:00 19:20:59 3 7.0 11.1 666.2 194.2 22.502/24/10 02/24/10 19:21:02 19:21:57 3 7.0 11.1 667.1 194.1 18.702/24/10 02/24/10 19:22:00 19:22:58 3 7.0 11.1 668.3 194.3 19.502/24/10 02/24/10 19:23:01 19:23:59 3 6.9 11.1 671.1 194.1 21.902/24/10 02/24/10 19:24:02 19:24:57 3 6.9 11.1 672.4 194.3 26.702/24/10 02/24/10 19:25:01 19:25:59 3 6.8 11.1 672.7 194.6 26.502/24/10 02/24/10 19:26:02 19:26:57 3 6.9 11.0 669.9 194.1 24.902/24/10 02/24/10 19:27:00 19:27:58 3 6.9 11.0 669.9 193.6 18.002/24/10 02/24/10 19:28:01 19:28:59 3 7.0 11.0 669.1 194.0 16.302/24/10 02/24/10 19:29:02 19:29:58 3 7.0 11.0 668.3 194.2 17.802/24/10 02/24/10 19:30:01 19:30:59 3 7.0 11.0 670.4 194.4 18.802/24/10 02/24/10 19:31:02 19:31:57 3 7.0 11.0 670.6 193.7 16.702/24/10 02/24/10 19:32:00 19:32:58 3 6.9 11.1 673.4 193.6 16.602/24/10 02/24/10 19:33:01 19:33:59 3 6.8 11.1 673.7 194.1 16.9
Start Date End Date Start Test Stop O2 CO2 SO2 NOx CO

% ppm % ppm ppm

02/24/10 02/24/10 19:34:02 19:34:58 3 6.9 11.1 673.6 194.0 18.7

Average 6.9 11.1 664.2 199.7 13.7

Minimum Value

Maximum Value

6.3 10.4 600.2 175.6 -9.28.2 12.0 679.1 209.2 27.4
Calibration Report

NRG

Vienna

Unit: 8

Channel Test # Z/M/H Local/S Start Time Stop Time ys Bias Actual Value Cylinder Value Span

O2 07:37:03 07:37:15 20 1 Zero Local 0.00 0.00

O2 07:46:27 07:46:39 20 1 Mid Local 10.00 9.97

O2 07:45:04 07:45:16 20 1 High Local 20.00 20.00

O2 08:07:01 08:07:13 20 1 Zero Pre SB 0.00 0.00

O2 08:23:21 08:23:33 20 1 Mid Pre SB 10.00 9.97

O2 12:02:48 12:03:00 20 1 Zero Post SB 0.00 0.00

O2 12:15:29 12:15:38 20 1 Mid Post SB 10.00 9.97

O2 16:21:08 16:21:54 20 2 Zero Post SB 0.06 0.00

O2 16:27:43 16:27:55 20 2 Mid Post SB 10.00 9.97

O2 19:41:14 19:41:26 20 3 Zero Post SB 0.00 0.00

O2 19:49:58 19:50:10 20 3 Mid Post SB 10.00 9.97

CO2 07:37:03 07:37:15 19.32 1 Zero Local 0.00 0.00

CO2 07:46:27 07:46:39 19.32 1 Mid Local 10.00 10.00

CO2 07:45:04 07:45:16 19.32 1 High Local 19.28 19.32

CO2 08:07:04 08:07:13 19.32 1 Zero Pre SB 0.00 0.00

CO2 08:23:24 08:23:36 19.32 1 Mid Pre SB 9.98 10.00

CO2 12:02:48 12:03:00 19.32 1 Zero Post SB 0.00 0.00

CO2 12:15:29 12:15:41 19.32 1 Mid Post SB 10.00 10.00

CO2 16:21:05 16:21:50 19.32 2 Zero Post SB 0.00 0.00

CO2 16:27:24 16:27:33 19.32 2 Mid Post SB 10.10 10.00

CO2 19:41:14 19:41:26 19.32 3 Zero Post SB 0.10 0.00

CO2 19:49:58 19:50:10 19.32 3 Mid Post SB 10.10 10.00

SO2 07:45:04 07:46:39 800.3 1 Zero Local 0.20 0.00

SO2 07:58:38 07:58:51 800.3 1 Mid Local 400.60 399.50

SO2 08:01:30 08:01:42 800.3 1 High Local 798.40 800.30

SO2 08:29:07 08:29:19 800.3 1 Zero Pre SB 5.40 0.00

SO2 08:20:18 08:20:30 800.3 1 Mid Pre SB 401.00 399.50

SO2 12:17:37 12:17:46 800.3 1 Zero Post SB 1.00 0.00

SO2 12:05:33 12:05:45 800.3 1 Mid Post SB 402.80 399.50

SO2 16:32:03 16:32:37 800.3 2 Zero Post SB 3.30 0.00

SO2 16:21:05 16:21:50 800.3 2 Mid Post SB 400.50 399.50

SO2 19:50:01 19:50:34 800.3 3 Zero Post SB 4.70 0.00

SO2 19:41:17 19:41:26 800.3 3 Mid Post SB 399.75 399.50

NOx 07:45:04 07:46:39 400.2 1 Zero Local 0.30 0.00

NOx 07:50:59 07:51:12 400.2 1 Mid Local 203.00 203.00

NOx 07:58:38 07:58:48 400.2 1 High Local 400.00 400.20

NOx 08:29:07 08:29:19 400.2 1 Zero Pre SB 0.90 0.00

NOx 08:11:23 08:11:35 400.2 1 Mid Pre SB 202.60 203.00

NOx 12:17:37 12:17:49 400.2 1 Zero Post SB 0.60 0.00

NOx 12:08:02 12:08:14 400.2 1 Mid Post SB 202.90 203.00

NOx 16:27:18 16:27:30 400.2 2 Zero Post SB 0.70 0.00

NOx 16:23:13 16:23:25 400.2 2 Mid Post SB 202.20 203.00

NOx 19:50:25 19:50:37 400.2 3 Zero Post SB 0.50 0.00

NOx 19:43:26 19:43:38 400.2 3 Mid Post SB 203.30 203.00

CO 07:45:04 07:46:33 203 1 Zero Local 0.38 0.00

CO 07:48:26 07:48:38 203 1 Mid Local 99.80 99.80

CO 07:51:02 07:51:15 203 1 High Local 203.20 203.00

CO 08:29:07 08:29:19 203 1 Zero Pre SB 0.20 0.00

CO 08:06:24 08:06:36 203 1 Mid Pre SB 98.20 99.80

CO 12:19:38 12:19:47 203 1 Zero Post SB 2.25 0.00

CO 12:11:22 12:11:35 203 1 Mid Post SB 100.40 99.80

CO 16:27:18 16:28:53 203 2 Zero Post SB 2.43 0.00

CO 16:25:34 16:25:46 203 2 Mid Post SB 100.20 99.80
Channel Test # Z/M/H Local/Sys Bias Actual Value Cylinder Value Start Time Stop Time Span

CO 19:50:34 19:50:47 203 3 Zero Post SB 1.00 0.00

CO 19:45:40 19:45:52 203 3 Mid Post SB 97.80 99.80
Or Alternate Method

NOx Converter Efficiency Test

NO2 Gas

Valve

NOx Highest Peak (ppm)

NOx End of Test (ppm)

Directions: Fill a Tedlar bag with the mid value 

NOx and the 20% O2 about 50/50. Connect 

the bag immediately to the NOx analyzer 

directly in the back for 30 minutes.

NOx Converter Efficiency

< 2% Allowed

Date

Start Time

End Time

Directions: Introduce NO2 Protocol 1 

calibration gas directly into the analyzer in NOx

mode. Gas must be between 40 to 60 ppm. 

Pass >= 90% Allowed

100.52 NOx Converter Efficiency

End Time

Start Time

Date

NOx Stable Reading (ppm

NOx Bottle Value (ppm)
Vienna

Emission Report

NRG

Unit: 8

Start Date NOx End Date Start Test Stop

ppm

02/24/10 02/24/10 20:00:00 20:00:59 4 51.702/24/10 02/24/10 20:01:02 20:01:57 4 51.602/24/10 02/24/10 20:02:00 20:02:58 4 51.602/24/10 02/24/10 20:03:01 20:03:59 4 51.902/24/10 02/24/10 20:04:02 20:04:57 4 52.0

Average 51.8

Minimum Value

Maximum Value

51.652.0

CERTIFICATE OF ANALYSIS

Grade of Product: EPA Protocol

Customer: CRAFTON

Part Number: E02NI99E15A1505 Reference Number: 32-112019271-3

Cylinder Number: CC312673 Cylinder Volume: 144 Cu.Ft.

Laboratory: MIC - Royal Oak-32 - MI Cylinder Pressure: 2015 PSIG

Analysis Date: Jan 26, 2010 Valve Outlet: 350

Expiration Date: Jan 26, 2013

Certification performed in accordance with "EPA Traceability Protocol (Sept. 1997)" using the assay procedures listed. Analytical Methodology does not require correction for

analytical interferences. This cylinder has a total analytical uncertainty as stated below with a confidence level of 95%. There are no significant impurities which affect the use

of this calibration mixture. All concentrations are on a volume/volume basis unless otherwise noted.

Do Not Use This Cylinder below 150 psig.i.e. 1 Mega Pascal

ANALYTICAL RESULTS

Component Requested Actual Protocol Total Relative

Concentration Concentration Method Uncertainty

PROPANE 15.00 PPM 15.12 PPM G1 +/- 1% NIST Traceable

NITROGEN Balance

CALIBRATION STANDARDS

Type Lot ID Cylinder No Concentration Expiration Date

NTRM 00060607 XC003550B 30.0PPM PROPANE/AIR Sep 02, 2010

ANALYTICAL EQUIPMENT

Instrument/Make/Model Analytical Principle Last Multipoint Calibration

E/N 54, 50ppmFS C3H8, Nicolet 6700 Fourier Transform Infrared (FTIR) Dec 29, 2009

Triad Data Available Upon Request

Notes:

Signature on file

____________________________________

QA Approval

Page 1 of 32-112019271-3
CERTIFICATE OF ANALYSIS

Grade of Product: EPA Protocol

Customer: PITTSBURGH / CRAFTON

Part Number: E03NI99E15A1364 Reference Number: 32-112875645-3

Cylinder Number: CC210119 Cylinder Volume: 144 Cu.Ft.

Laboratory: MIC - Royal Oak-32 - MI Cylinder Pressure: 2015 PSIG

Analysis Date: Jul 28, 2009 Valve Outlet: 660

Expiration Date: Jul 28, 2011

Certification performed in accordance with "EPA Traceability Protocol (Sept. 1997)" using the assay procedures listed. Analytical Methodology does not require correction for

analytical interferences. This cylinder has a total analytical uncertainty as stated below with a confidence level of 95%. There are no significant impurities which affect the use

of this calibration mixture. All concentrations are on a volume/volume basis unless otherwise noted.

Do Not Use This Cylinder below 150 psig.i.e. 1 Mega Pascal

ANALYTICAL RESULTS

Component Requested Actual Protocol Total Relative

Concentration Concentration Method Uncertainty

NITRIC OXIDE 800.0 PPM 781.5 PPM G1 +/- 1% NIST Traceable

SULFUR DIOXIDE 800.0 PPM 800.3 PPM G1 +/- 1% NIST Traceable

NITROGEN Balance

Total oxides of nitrogen 782.4 PPM For Reference Only

CALIBRATION STANDARDS

Type Lot ID Cylinder No Concentration Expiration Date

NTRM 08060608 CC255471 1025.3PPM NITRIC OXIDE/NITROGEN May 01, 2012

NTRM 01050311 SG9151303BAL 996.6PPM SULFUR DIOXIDE/NITROGEN Aug 15, 2009

NTRM 01050311 SG9151303BAL 996.6PPM SULFUR DIOXIDE/NITROGEN May 01, 2011

ANALYTICAL EQUIPMENT

Instrument/Make/Model Analytical Principle Last Multipoint Calibration

E/N 54, 1000 ppmFS NO, Nicolet 6700 Fourier Transform Infrared (FTIR) Jul 02, 2009

E/N 54, 1000ppmFS SO2, Nicolet 6700 Fourier Transform Infrared (FTIR) Jul 02, 2009

Triad Data Available Upon Request

Notes:

Signature on file

____________________________________

QA Approval

Page 1 of 32-112875645-3
CERTIFICATE OF ANALYSIS

Grade of Product: EPA Protocol

Customer: PITTS/CRAFTON

Part Number: E03NI61E15A37R4 Reference Number: 32-112836750-1

Cylinder Number: CC201217 Cylinder Volume: 159 Cu.Ft.

Laboratory: MIC - Royal Oak-32 - MI Cylinder Pressure: 2015 PSIG

Analysis Date: Apr 21, 2009 Valve Outlet: 590

Expiration Date: Apr 21, 2012

Certification performed in accordance with "EPA Traceability Protocol (Sept. 1997)" using the assay procedures listed. Analytical Methodology does not require correction for

analytical interferences. This cylinder has a total analytical uncertainty as stated below with a confidence level of 95%. There are no significant impurities which affect the use

of this calibration mixture. All concentrations are on a volume/volume basis unless otherwise noted.

Do Not Use This Cylinder below 150 psig.i.e. 1 Mega Pascal

ANALYTICAL RESULTS

Component Requested Actual Protocol Total Relative

Concentration Concentration Method Uncertainty

CARBON DIOXIDE 19.00 % 19.32 % G1 +/- 1% NIST Traceable

OXYGEN 20.00 % 20.00 % G1 +/- 1% NIST Traceable

NITROGEN Balance

CALIBRATION STANDARDS

Type Lot ID Cylinder No Concentration Expiration Date

NTRM 06060803 CC206012 22.51% OXYGEN/NITROGEN May 01, 2010

NTRM 04060434 XC034411B 19.84% CARBON DIOXIDE/NITROGEN May 15, 2012

ANALYTICAL EQUIPMENT

Instrument/Make/Model Analytical Principle Last Multipoint Calibration

E/N 54, 20% FS CO2, Nicolet 6700 Fourier Transform Infrared (FTIR) Apr 03, 2009

E/N 51, 25%FS O2, Rosemont 755R Paramagnetic (Para) Apr 10, 2009

Triad Data Available Upon Request

Notes:Order#419110

Signature on file

____________________________________

QA Approval

Page 1 of 32-112836750-1
CERTIFICATE OF ANALYSIS

Grade of Product: EPA Protocol

Customer: CRAFTON

Part Number: E02NI99E15A1965 Reference Number: 32-112019271-5

Cylinder Number: CC48993 Cylinder Volume: 144 Cu.Ft.

Laboratory: MIC - Royal Oak-32 - MI Cylinder Pressure: 2015 PSIG

Analysis Date: Jan 26, 2010 Valve Outlet: 350

Expiration Date: Jan 26, 2013

Certification performed in accordance with "EPA Traceability Protocol (Sept. 1997)" using the assay procedures listed. Analytical Methodology does not require correction for

analytical interferences. This cylinder has a total analytical uncertainty as stated below with a confidence level of 95%. There are no significant impurities which affect the use

of this calibration mixture. All concentrations are on a volume/volume basis unless otherwise noted.

Do Not Use This Cylinder below 150 psig.i.e. 1 Mega Pascal

ANALYTICAL RESULTS

Component Requested Actual Protocol Total Relative

Concentration Concentration Method Uncertainty

PROPANE 26.00 PPM 26.02 PPM G1 +/- 1% NIST Traceable

NITROGEN Balance

CALIBRATION STANDARDS

Type Lot ID Cylinder No Concentration Expiration Date

NTRM 00060607 XC003550B 30.0PPM PROPANE/AIR Sep 02, 2010

ANALYTICAL EQUIPMENT

Instrument/Make/Model Analytical Principle Last Multipoint Calibration

E/N 54, 50ppmFS C3H8, Nicolet 6700 Fourier Transform Infrared (FTIR) Dec 29, 2009

Triad Data Available Upon Request

Notes:

Signature on file

____________________________________

QA Approval

Page 1 of 32-112019271-5
Close Window | Save As | Print

6141 EASTON ROAD, BLDG 1, PLUMSTEADVILLE, PA 18949-0310 Phone: 800-331-4953 Fax: 215-766-7226

RATA CLASS

Dual-Analyzed Calibration Standard

CERTIFICATE OF ACCURACY: Interference FreeTM Multi-Component EPA

Protocol Gas

Assay Laboratory Customer

AIR LIQUIDE AMERICA SPECIALTY GASES LLC P.O. No.: 1197 EAGLE MOUNTAIN SCIENTIFIC, INC.

6141 EASTON ROAD, BLDG 1 Project No.: 01-85673-002 PO#1197

PLUMSTEADVILLE, PA 18949-0310 321 PERRY HIGHWAY

 HARMONY PA 16037

ANALYTICAL INFORMATION

This certification was performed according to EPA Traceability Protocol For Assay & Certification of Gaseous Calibration Standards; Procedure G-1; September, 1997.

Cylinder Number: ALM058516 Certification Date: 03Jul2008 Exp. Date: 03Jul2010

Cylinder Pressure***: 1969 PSIG

 

COMPONENT CERTIFIED CONCENTRATION (Moles) ACCURACY** TRACEABILITY

CARBON MONOXIDE 99.8  PPM +/- 1% Direct NIST and VSL

NITRIC OXIDE 103.1  PPM +/- 1% Direct NIST and VSL

SULFUR DIOXIDE * 98.8  PPM +/- 1% Direct NIST and VSL

NITROGEN - OXYGEN FREE  BALANCE

 

TOTAL OXIDES OF NITROGEN 103.3  PPM Reference Value Only

*** Do not use when cylinder pressure is below 150 psig.

** Analytical accuracy is based on the requirements of EPA Protocol Procedure G1, September 1997.

REFERENCE STANDARD

TYPE/SRM NO. EXPIRATION DATE CYLINDER NUMBER CONCENTRATION COMPONENT

NTRM 1679 02Oct2010 KAL003176 101.0 PPM CARBON MONOXIDE

NTRM 1684 01Sep2010 KAL003309 97.68 PPM NITRIC OXIDE

NTRM 1694 15Aug2009 ALM012796 97.81 PPM SULFUR DIOXIDE

INSTRUMENTATION

INSTRUMENT/MODEL/SERIAL# DATE LAST CALIBRATED ANALYTICAL PRINCIPLE

FTIR//000928781 20Jun2008 FTIR

FTIR//000928781 24Jun2008 FTIR

FTIR//000928781 27Jun2008 FTIR

ANALYZER READINGS

(Z=Zero Gas R=Reference Gas T=Test Gas r=Correlation Coefficient)

First Triad Analysis Second Triad Analysis Calibration Curve

CARBON MONOXIDE

Date: 25Jun2008 Response Unit: PPM Date: 03Jul2008 Response Unit: PPM Concentration=A+Bx+Cx2+Dx3+Ex4

Z1=0.03689  R1=101.0326 T1=99.84225 Z1=0.01015  R1=101.2590 T1=100.1089 r=9.99996E-1 

R2=101.1695 Z2=0.04651  T2=99.92941 R2=101.3840 Z2=0.01034  T2=100.1785 Constants: A=0.00000E+0

Z3=0.16511  T3=100.0977 R3=101.3606 Z3=0.07190  T3=100.2326 R3=101.4701 B=8.90380E-1  C=3.69000E-4

Avg. Concentration: 99.77 PPM Avg. Concentration: 99.81 PPM D=0.00000E+0  E=0.00000E+0

NITRIC OXIDE

Date: 25Jun2008 Response Unit: PPM Date: 03Jul2008 Response Unit: PPM Concentration=A+Bx+Cx2+Dx3+Ex4

Z1=-0.10888 R1=97.48216 T1=102.5818 Z1=-0.34075 R1=97.11698 T1=102.7954 r=9.99999E-1 

R2=97.57177 Z2=-0.07875 T2=102.7965 R2=97.29479 Z2=-0.30919 T2=103.0190 Constants: A=0.00000E+0

Z3=0.14515  T3=102.9802 R3=97.75097 Z3=0.11823  T3=103.0996 R3=97.58145 B=9.78844E-1  C=4.40000E-5

Avg. Concentration: 102.9 PPM Avg. Concentration: 102.9 PPM D=0.00000E+0  E=0.00000E+0

SULFUR DIOXIDE *

Date: 25Jun2008 Response Unit: PPM Date: 03Jul2008 Response Unit: PPM Concentration=A+Bx+Cx2+Dx3+Ex4

Scott's Customer Online Information System http://www.scottecatalog.com/eScott2.nsf/(Cert)?OpenAgent&UNID=25...

1 of 2 5/3/2010 5:11 PM
Z1=-0.03004 R1=98.32191 T1=99.23911 Z1=-0.02136 R1=98.10413 T1=99.18566 r=9.99999E-1 

R2=98.35784 Z2=-0.01142 T2=99.32192 R2=98.22753 Z2=-0.01519 T2=99.20294 Constants: A=0.00000E+0

Z3=-0.00934 T3=99.35703 R3=98.39039 Z3=0.00042  T3=99.20499 R3=98.30937 B=9.97351E-1  C=1.70000E-5

Avg. Concentration: 98.75 PPM Avg. Concentration: 98.79 PPM D=0.00000E+0  E=0.00000E+0

QUALITY ASSURANCE

APPROVED BY: James M. Lunger

(signature on file)

Scott's Customer Online Information System http://www.scottecatalog.com/eScott2.nsf/(Cert)?OpenAgent&UNID=25...

2 of 2 5/3/2010 5:11 PM
Close Window | Save As | Print

6141 EASTON ROAD, BLDG 1, PLUMSTEADVILLE, PA 18949-0310 Phone: 800-331-4953 Fax: 215-766-7226

RATA CLASS

Dual-Analyzed Calibration Standard

CERTIFICATE OF ACCURACY: EPA Protocol Gas

Assay Laboratory Customer

AIR LIQUIDE AMERICA SPECIALTY GASES LLC P.O. No.: 2191 EAGLE MOUNTAIN SCIENTIFIC, INC.

6141 EASTON ROAD, BLDG 1 Project No.: 01 -10574 -001 PO#2191

PLUMSTEADVILLE, PA 18949-0310 321 PERRY HIGHWAY

 HARMONY PA 16037

ANALYTICAL INFORMATION

This certification was performed according to EPA Traceability Protocol For Assay & Certification of Gaseous Calibration Standards; Procedure G-1; September, 1997.

Cylinder Number: ALM054263 Certification Date: 08Sep2009 Exp. Date: 07Sep2012

Cylinder Pressure***: 2000 PSIG

 

COMPONENT CERTIFIED CONCENTRATION (Moles) ACCURACY** TRACEABILITY

CARBON DIOXIDE 10.0 % +/- 1% Direct NIST and VSL

OXYGEN 9.97 % +/- 1% Direct NIST and VSL

NITROGEN  BALANCE

*** Do not use when cylinder pressure is below 150 psig.

** Analytical accuracy is based on the requirements of EPA Protocol Procedure G1, September 1997.

REFERENCE STANDARD

TYPE/SRM NO. EXPIRATION DATE CYLINDER NUMBER CONCENTRATION COMPONENT

NTRM 1675 02Oct2012 K001509 13.93 % CARBON DIOXIDE

NTRM 2658 01Jan2010 K001907 10.03 % OXYGEN

INSTRUMENTATION

INSTRUMENT/MODEL/SERIAL# DATE LAST CALIBRATED ANALYTICAL PRINCIPLE

MTI/M200/170927 12Aug2009 GC-TCD

MTI/M200/170927 01Sep2009 GC-TCD

ANALYZER READINGS

(Z=Zero Gas R=Reference Gas T=Test Gas r=Correlation Coefficient)

First Triad Analysis Second Triad Analysis Calibration Curve

CARBON DIOXIDE

Date: 08Sep2009 Response Unit: AREA Concentration=A+Bx+Cx2+Dx3+Ex4

Z1=0.00000  R1=591590.0 T1=426401.0 r=.9999978  2300

R2=592784.0 Z2=0.00000  T2=427190.0 Constants: A=-0.01502641

Z3=0.00000  T3=427225.0 R3=592724.0 B=2.35659E-05  C=

Avg. Concentration: 10.00 % D=  E=

OXYGEN

Date: 08Sep2009 Response Unit: AREA Concentration=A+Bx+Cx2+Dx3+Ex4

Z1=0.00000  R1=299568.0 T1=297767.0 r=.9999994  2350

R2=299591.0 Z2=0.00000  T2=297760.0 Constants: A=-0.00746265

Z3=0.00000  T3=297704.0 R3=299512.0 B=3.35338E-05  C=

Avg. Concentration: 9.970 % D=  E=

QUALITY ASSURANCE

APPROVED BY: JOHN C. FITZ

(signature on file)

Scott's Customer Online Information System http://www.scottecatalog.com/eScott2.nsf/(Cert)?OpenAgent&UNID=3D...

1 of 1 10/14/2009 2:24 PM
Close Window | Save As | Print

6141 EASTON ROAD, BLDG 1, PLUMSTEADVILLE, PA 18949-0310 Phone: 800-331-4953 Fax: 215-766-7226

RATA CLASS

Dual-Analyzed Calibration Standard

CERTIFICATE OF ACCURACY: Interference FreeTM Multi-Component EPA

Protocol Gas

Assay Laboratory Customer

AIR LIQUIDE AMERICA SPECIALTY GASES LLC P.O. No.: 2191 EAGLE MOUNTAIN SCIENTIFIC, INC.

6141 EASTON ROAD, BLDG 1 Project No.: 01-10574-002 PO#2191

PLUMSTEADVILLE, PA 18949-0310 321 PERRY HIGHWAY

 HARMONY PA 16037

ANALYTICAL INFORMATION

This certification was performed according to EPA Traceability Protocol For Assay & Certification of Gaseous Calibration Standards; Procedure G-1; September, 1997.

Cylinder Number: AAL6503 Certification Date: 04Sep2009 Exp. Date: 04Sep2011

Cylinder Pressure***: 1957 PSIG

 

COMPONENT CERTIFIED CONCENTRATION (Moles) ACCURACY** TRACEABILITY

CARBON MONOXIDE 203  PPM +/- 1% Direct NIST and VSL

NITRIC OXIDE 203  PPM +/- 1% Direct NIST and VSL

SULFUR DIOXIDE * 200  PPM +/- 1% Direct NIST and VSL

NITROGEN - OXYGEN FREE  BALANCE

 

TOTAL OXIDES OF NITROGEN 203.  PPM Reference Value Only

*** Do not use when cylinder pressure is below 150 psig.

** Analytical accuracy is based on the requirements of EPA Protocol Procedure G1, September 1997.

REFERENCE STANDARD

TYPE/SRM NO. EXPIRATION DATE CYLINDER NUMBER CONCENTRATION COMPONENT

NTRM 2636 02Oct2011 KAL003735 240.8 PPM CARBON MONOXIDE

NTRM 1685 01Sep2010 KAL003529 247.1 PPM NITRIC OXIDE

NTRM 0260 26 15Jan2012 KAL003834 255.5 PPM SULFUR DIOXIDE

INSTRUMENTATION

INSTRUMENT/MODEL/SERIAL# DATE LAST CALIBRATED ANALYTICAL PRINCIPLE

FTIR//000928781 13Aug2009 FTIR

FTIR//000928781 03Sep2009 FTIR

FTIR//000928781 20Aug2009 FTIR

ANALYZER READINGS

(Z=Zero Gas R=Reference Gas T=Test Gas r=Correlation Coefficient)

First Triad Analysis Second Triad Analysis Calibration Curve

CARBON MONOXIDE

Date: 28Aug2009 Response Unit: PPM Date: 04Sep2009 Response Unit: PPM Concentration=A+Bx+Cx2+Dx3+Ex4

Z1=-0.06717 R1=240.7736 T1=203.1505 Z1=0.00026  R1=240.7769 T1=203.2147 r=9.99998E-1 

R2=240.8373 Z2=0.04613  T2=203.1897 R2=240.7849 Z2=0.14359  T2=203.2278 Constants: A=0.00000E+0

Z3=0.11289  T3=203.2159 R3=241.0262 Z3=0.20849  T3=203.4315 R3=240.9072 B=6.40608E-1  C=1.93000E-4

Avg. Concentration: 203.1 PPM Avg. Concentration: 203.3 PPM D=0.00000E+0  E=0.00000E+0

NITRIC OXIDE

Date: 28Aug2009 Response Unit: PPM Date: 04Sep2009 Response Unit: PPM Concentration=A+Bx+Cx2+Dx3+Ex4

Z1=0.05072  R1=247.2781 T1=202.9109 Z1=-0.36966 R1=246.8645 T1=202.3796 r=9.99998E-1 

R2=247.3229 Z2=0.12835  T2=203.0468 R2=247.0825 Z2=0.08026  T2=202.6763 Constants: A=0.00000E+0

Z3=0.13283  T3=203.2857 R3=247.6443 Z3=0.09755  T3=202.7391 R3=247.3359 B=8.86440E-1  C=3.90000E-5

Avg. Concentration: 202.8 PPM Avg. Concentration: 202.6 PPM D=0.00000E+0  E=0.00000E+0

SULFUR DIOXIDE *

Date: 28Aug2009 Response Unit: PPM Date: 04Sep2009 Response Unit: PPM Concentration=A+Bx+Cx2+Dx3+Ex4

Scott's Customer Online Information System http://www.scottecatalog.com/eScott2.nsf/(Cert)?OpenAgent&UNID=25...

1 of 2 5/3/2010 5:12 PM
Z1=-0.02802 R1=254.2538 T1=199.0511 Z1=-0.08905 R1=254.0888 T1=199.4037 r=9.99994E-1 

R2=254.3715 Z2=-0.00186 T2=199.3638 R2=254.1315 Z2=-0.04392 T2=199.4893 Constants: A=0.00000E+0

Z3=0.07003  T3=199.4671 R3=254.4009 Z3=0.01164  T3=199.4941 R3=254.3046 B=9.98684E-1  C=5.00000E-6

Avg. Concentration: 200.2 PPM Avg. Concentration: 200.5 PPM D=0.00000E+0  E=0.00000E+0

QUALITY ASSURANCE

APPROVED BY: James M. Lunger

(signature on file)

Scott's Customer Online Information System http://www.scottecatalog.com/eScott2.nsf/(Cert)?OpenAgent&UNID=25...

2 of 2 5/3/2010 5:12 PM
CERTIFICATE OF ANALYSIS

Grade of Product: EPA Protocol

Customer: CRAFTON

Part Number: E02NI99E15A00P7 Reference Number: 32-112019271-1

Cylinder Number: EB0013468 Cylinder Volume: 144 Cu.Ft.

Laboratory: MIC - Royal Oak-32 - MI Cylinder Pressure: 2015 PSIG

Analysis Date: Jan 26, 2010 Valve Outlet: 350

Expiration Date: Jan 26, 2013

Certification performed in accordance with "EPA Traceability Protocol (Sept. 1997)" using the assay procedures listed. Analytical Methodology does not require correction for

analytical interferences. This cylinder has a total analytical uncertainty as stated below with a confidence level of 95%. There are no significant impurities which affect the use

of this calibration mixture. All concentrations are on a volume/volume basis unless otherwise noted.

Do Not Use This Cylinder below 150 psig.i.e. 1 Mega Pascal

ANALYTICAL RESULTS

Component Requested Actual Protocol Total Relative

Concentration Concentration Method Uncertainty

PROPANE 43.00 PPM 43.13 PPM G1 +/- 1% NIST Traceable

NITROGEN Balance

CALIBRATION STANDARDS

Type Lot ID Cylinder No Concentration Expiration Date

NTRM 08061018 CC263008 49.62PPM PROPANE/NITROGEN Jul 15, 2012

ANALYTICAL EQUIPMENT

Instrument/Make/Model Analytical Principle Last Multipoint Calibration

E/N 54, 50ppmFS C3H8, Nicolet 6700 Fourier Transform Infrared (FTIR) Dec 29, 2009

Triad Data Available Upon Request

Notes:

Signature on file

____________________________________

QA Approval

Page 1 of 32-112019271-1
Calibration Report

NRG

Vienna

Unit: 8

Channel Test # Z/M/H Local/S Start Time Stop Time ys Bias Actual Value Cylinder Value Span

THC 07:50:48 07:52:18 45 1 Zero Local 0.20 0.00

THC 07:54:53 07:55:05 45 1 Mid Local 15.46 15.12

THC 08:00:13 08:00:34 45 1 High Local 42.99 43.13

THC 12:03:44 12:04:54 45 1 Zero Post SB 0.26 0.00

THC 12:07:31 12:07:40 45 1 Mid Post SB 15.30 15.12

THC 12:10:14 12:10:38 45 1 High Post SB 42.70 43.13

THC 15:41:08 15:41:20 45 2 Zero Post SB 0.16 0.00

THC 15:47:23 15:48:11 45 2 Mid Post SB 15.14 15.12

THC 15:44:03 15:45:43 45 2 High Post SB 42.70 43.13

THC 18:43:42 18:43:51 45 3 Zero Post SB 0.52 0.00

THC 18:45:43 18:46:10 45 3 Mid Post SB 15.03 15.12

THC 18:51:10 18:51:43 45 3 High Post SB 42.58 43.13
Calibration Report

NRG

Vienna

Unit: 8

Channel Test # Z/M/H Local/S Start Time Stop Time ys Bias Actual Value Cylinder Value Span

THC 07:50:48 07:52:18 45 1 Zero Local 0.20 0.00

THC 07:57:09 07:57:24 45 1 Mid Local 26.14 26.02

THC 08:00:13 08:00:34 45 1 High Local 42.99 43.13

THC 12:03:44 12:04:54 45 1 Zero Post SB 0.26 0.00

THC 12:12:18 12:12:30 45 1 Mid Post SB 26.64 26.02

THC 12:10:14 12:10:38 45 1 High Post SB 42.70 43.13

THC 15:41:08 15:41:20 45 2 Zero Post SB 0.16 0.00

THC 15:38:18 15:38:31 45 2 Mid Post SB 26.42 26.02

THC 15:44:03 15:45:43 45 2 High Post SB 42.70 43.13

THC 18:43:42 18:43:51 45 3 Zero Post SB 0.52 0.00

THC 18:48:27 18:48:54 45 3 Mid Post SB 25.00 26.02

THC 18:51:10 18:51:43 45 3 High Post SB 42.58 43.13
Emission Report

THC 

Test Stop

ppm

9:50:56 1 14.69:51:58 1 14.5

9:52:58 1 14.5

9:53:59 1 14.49:54:59 1 14.5

9:55:57 1 14.7

9:56:57 1 15.59:57:58 1 14.7

9:58:58 1 14.8

9:59:58 1 20.00:00:59 1 18.3

0:01:59 1 14.9

0:02:57 1 14.30:03:57 1 14.4

0:04:57 1 15.4

0:05:58 1 15.50:06:59 1 14.8

0:07:59 1 14.3

0:08:59 1 14.00:09:57 1 14.0

0:10:58 1 13.9

0:11:58 1 14.20:12:59 1 14.1

0:13:59 1 14.3

0:14:57 1 14.70:15:57 1 15.2

0:16:58 1 15.5

0:17:58 1 14.30:18:59 1 14.7

0:19:59 1 14.7

0:20:57 1 14.6
THC 

Test Sto

p

pp

m

0:21:57 1 14.50:22:58 1 15.00:23:58 1 15.00:24:58 1 15.10:25:59 1 14.40:26:59 1 14.30:27:57 1 15.20:28:57 1 14.80:29:58 1 14.10:30:58 1 14.60:31:59 1 14.50:32:59 1 14.50:33:59 1 14.00:34:57 1 14.10:35:57 1 14.40:36:58 1 15.20:37:58 1 14.80:38:59 1 14.70:39:59 1 15.60:40:59 1 15.60:41:57 1 16.10:42:57 1 15.60:43:58 1 15.00:44:58 1 15.00:45:59 1 14.90:46:59 1 14.50:47:57 1 15.00:48:57 1 14.70:49:58 1 14.50:50:58 1 14.50:51:59 1 14.40:52:59 1 14.50:53:59 1 14.80:54:57 1 14.30:55:57 1 14.00:56:58 1 14.10:57:58 1 15.0
THC 

Test Sto

p

pp

m

0:58:59 1 14.30:59:59 1 14.61:00:57 1 14.71:01:57 1 14.91:02:57 1 15.11:03:58 1 14.71:04:58 1 14.11:05:59 1 14.01:06:59 1 14.71:07:57 1 15.31:08:57 1 15.21:09:58 1 15.11:10:58 1 14.41:11:58 1 14.71:12:59 1 14.41:13:59 1 14.91:14:57 1 14.31:15:57 1 14.61:16:58 1 14.41:17:58 1 14.41:18:58 1 14.81:19:59 1 14.81:20:59 1 14.21:21:57 1 14.51:22:57 1 14.91:23:58 1 14.61:24:58 1 14.51:25:58 1 14.61:26:59 1 15.01:27:59 1 14.31:28:57 1 14.51:29:57 1 15.01:30:58 1 15.11:31:58 1 14.81:32:59 1 15.41:33:59 1 14.71:34:57 1 14.8
THC 

Test Sto

p

pp

m

1:35:57 1 15.21:36:58 1 14.71:37:58 1 14.61:38:58 1 14.51:39:59 1 15.11:40:59 1 15.71:41:57 1 15.21:42:57 1 15.61:43:58 1 14.91:44:58 1 14.71:45:59 1 14.81:46:59 1 14.51:47:57 1 14.91:48:57 1 14.71:49:58 1 15.3

14.8

13.920.0
Emission Report

THC 

Test Stop

ppm

3:07:58 2 10.13:08:59 2 10.3

3:09:59 2 10.2

3:10:57 2 10.43:11:57 2 10.1

3:12:57 2 10.4

3:13:58 2 10.33:14:58 2 10.0

3:15:59 2 10.3

3:16:59 2 10.23:17:57 2 10.3

3:18:57 2 10.0

3:19:58 2 10.43:20:58 2 10.4

3:21:59 2 10.2

3:22:59 2 10.33:23:59 2 10.6

3:24:57 2 10.4

3:25:58 2 10.43:26:58 2 10.2

3:27:59 2 10.3

3:28:59 2 10.43:29:59 2 10.0

3:30:57 2 10.1

3:31:57 2 10.03:32:58 2 10.1

3:33:58 2 10.2

3:34:59 2 10.33:35:59 2 10.2

3:36:57 2 10.0

3:37:57 2 10.3
THC 

Test Sto

p

pp

m

3:38:58 2 10.33:39:58 2 10.53:40:58 2 10.43:41:59 2 10.53:42:59 2 10.63:43:57 2 10.63:44:57 2 10.63:45:58 2 10.53:46:58 2 10.33:47:59 2 10.23:48:59 2 10.43:49:57 2 10.33:50:57 2 10.23:51:57 2 10.33:52:58 2 10.43:53:58 2 10.13:54:59 2 10.43:55:59 2 10.33:56:57 2 10.03:57:57 2 10.03:58:58 2 10.13:59:58 2 10.04:00:58 2 13.94:01:59 2 10.74:02:59 2 11.04:03:57 2 10.54:04:57 2 10.34:05:58 2 10.24:06:58 2 10.94:07:58 2 10.44:08:59 2 10.24:09:59 2 10.44:10:57 2 10.24:11:57 2 10.24:12:58 2 10.0

4:13:58 2 9.44:14:59 2 9.8
THC 

Test Sto

p

pp

m

4:15:59 2 10.54:16:57 2 10.84:17:57 2 10.34:18:57 2 10.34:19:58 2 10.54:20:58 2 10.54:21:59 2 10.24:22:59 2 10.04:23:57 2 10.1

4:24:57 2 9.74:25:58 2 9.74:26:58 2 9.6

4:27:59 2 10.24:28:56 2 10.14:29:57 2 10.24:30:58 2 10.1

4:31:58 2 9.84:32:59 2 9.9

4:33:59 2 10.4

4:34:57 2 9.84:35:57 2 9.74:36:58 2 9.44:37:58 2 9.24:38:59 2 9.84:39:59 2 9.54:40:57 2 9.24:41:57 2 9.54:42:58 2 8.94:43:58 2 9.14:44:59 2 9.64:45:59 2 9.54:46:57 2 9.24:47:57 2 9.24:48:58 2 9.34:49:58 2 9.14:50:59 2 9.04:51:59 2 8.9
THC 

Test Sto

p

pp

m

4:52:57 2 8.74:53:57 2 8.94:54:58 2 9.14:55:58 2 9.34:56:59 2 8.94:57:59 2 9.54:58:57 2 9.1

4:59:57 2 12.8

5:00:58 2 9.95:01:58 2 9.35:02:59 2 9.35:03:59 2 9.85:04:57 2 9.85:05:57 2 9.45:06:45 2 9.4

10.0

8.7

13.9
Emission Report

THC 

Test Stop

ppm

6:39:59 3 7.56:40:57 3 7.2

6:41:57 3 7.6

6:42:57 3 7.46:43:58 3 7.6

6:44:58 3 7.6

6:45:59 3 8.16:46:59 3 8.7

6:47:57 3 8.4

6:48:57 3 8.36:49:58 3 8.0

6:50:58 3 7.9

6:51:59 3 7.96:52:59 3 7.9

6:53:56 3 8.4

6:54:57 3 8.06:55:57 3 8.2

6:56:58 3 8.1

6:57:58 3 8.36:58:59 3 8.0

6:59:59 3 8.1

7:00:57 3 8.17:01:57 3 7.8

7:02:58 3 7.8

7:03:58 3 7.97:04:59 3 7.9

7:05:59 3 8.2

7:06:57 3 7.87:07:57 3 7.9

7:08:58 3 8.4

7:09:58 3 8.4
THC 

Test Sto

p

pp

m

7:10:59 3 10.57:11:59 3 8.87:12:57 3 8.57:13:57 3 8.87:14:58 3 8.37:15:58 3 8.37:16:59 3 8.27:17:59 3 8.27:18:57 3 8.97:19:57 3 8.67:20:57 3 8.27:21:58 3 8.57:22:58 3 8.57:23:59 3 8.57:24:59 3 8.57:25:57 3 8.77:26:57 3 8.87:27:58 3 8.47:28:58 3 8.37:29:58 3 8.67:30:59 3 8.47:31:59 3 8.47:32:57 3 8.17:33:57 3 8.57:34:58 3 8.47:35:58 3 8.47:36:58 3 8.37:37:59 3 8.37:38:59 3 8.17:39:57 3 10.17:40:57 3 9.57:41:58 3 8.87:42:58 3 8.47:43:59 3 8.27:44:59 3 8.27:45:57 3 7.77:46:57 3 8.0
THC 

Test Sto

p

pp

m

7:47:58 3 7.77:48:58 3 7.57:49:59 3 7.57:50:59 3 7.37:51:57 3 7.17:52:57 3 8.87:53:58 3 8.07:54:59 3 7.57:55:59 3 7.47:56:57 3 7.17:57:57 3 7.27:58:58 3 7.27:59:58 3 7.48:00:59 3 7.58:01:59 3 7.48:02:57 3 7.48:03:57 3 7.58:04:58 3 7.58:05:58 3 7.38:06:59 3 7.68:07:59 3 7.68:08:57 3 7.48:09:57 3 7.58:10:58 3 7.58:11:58 3 7.88:12:59 3 8.28:13:56 3 7.38:14:57 3 7.28:15:58 3 7.08:16:58 3 7.4

8:17:59 3 10.9

8:18:59 3 7.68:19:57 3 7.48:20:57 3 7.28:21:58 3 7.28:22:58 3 7.28:23:59 3 7.5
THC 

Test Sto

p

pp

m

8:24:59 3 7.18:25:57 3 7.18:26:57 3 6.88:27:58 3 7.48:28:58 3 7.48:29:59 3 7.38:30:57 3 7.48:31:57 3 7.18:32:58 3 7.28:33:58 3 7.18:34:59 3 7.58:35:59 3 7.58:36:57 3 7.28:37:57 3 7.08:38:57 3 7.0

7.9

6.8

10.9