Name: Dana L. Rieves

Title: Compliance Supervisor

Company: James River Cogeneration Company

Sign Date:

Name: Lenny Katerynczuk

Title: Project Manager

Company: AirNova, Inc.

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Hopewell MACT ICR Testing Unit No. 2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 17, 2011 Page 1 of 23
Hopewell MACT ICR Testing Unit No. 2

Facility Information:

James River Cogeneration Company

912 East Randolph Road

Hopewell VA 23860

Contact: Dana L. Rieves

Phone:

Fax:

Email: danarieves@cogentrix.com

Testing Company:

AirNova, Inc.

5845 Clayton Avenue

Pennsauken NJ 08109

Contact:Lenny Katerynczuk

Phone: 856-486-1500

Fax: 856-486-9896

Email: lenny@airnova.com

Air Permit Number:

50950

Permitted Source ID/Name:

50950 James River Cogeneration Company

Permitted Maximum Process Rate:

200 MMBtu/hr (157,500 lbs steam/hr)

Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 1 consists of three (3) 200 million Btu heat input per hour bituminous coal-fired Foster Wheeler boilers. Each 

of the boilers that make up Unit 1 have a dedicated scrubber and bagfilter and are routed to a common turbine stack 

that is shared by all three boilers.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 5167000055 FRS #: 110000740422

SCC / Description 10100205 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Traveling Grate (Overfeed) Stoker (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 116 0 0 116 960 720 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Carbon Monoxide Method 10 3 180 0

Stack Exit Formaldehyde Method 0011 3 120 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit Method 202 3 120 0

Organic Condensible 

Particulate

Stack Exit Method 202 3 120 0

Regulation Description Compound Limit Unit

CAA Section 114 0

Thursday, February 17, 2011 Page 2 of 23
Hopewell MACT ICR Testing Unit No. 2

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None.

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Nickel Method 29 3 120 0

Stack Exit Arsenic Method 29 3 120 0

Stack Exit Beryllium Method 29 3 120 0

Stack Exit Chromium Method 29 3 120 0

Stack Exit Cadmium Method 29 3 120 0

Stack Exit Mercury Method 29 3 120 0

Stack Exit Manganese Method 29 3 120 0

Stack Exit Cobalt Method 29 3 120 0

Stack Exit Lead Method 29 3 120 0

Stack Exit Antimony Method 29 3 120 0

Stack Exit Selenium Method 29 3 120 0

Stack Exit Filterable Particulate Method 5 3 120 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Thursday, February 17, 2011 Page 3 of 23
Hopewell MACT ICR Testing Unit No. 2

Sampling / Stack Data Results Summary

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 5/6/2010 5/6/2010 5/6/2010

Run Start Time 8:35:00 AM 12:00:00 

PM

3:40:00 PM

Run Finish Time 10:44:00 AM 2:13:00 PM 5:51:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 84.478 81.799 80.217 82.165

Moisture Content of Stack Gas, % 10.95 10.55 10.56 10.687

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.34 13.09 13.59 13.340

Oxygen, % 6.05 5.87 5.44 5.787

Average Stack Gas Temperature, °F 220.58 228.33 230.25 226.387

Dry Volumetric Flow Rate, dry scfm 160,404.5 161,201.4 157,578.1 159,728.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,414.6 235,409.0 230,785.3 232,869.633

Percent Isokinetic of Sampling Rate, % 106.0 102.2 102.5 103.567

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 17, 2011 Page 4 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 202

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 17, 2011 Page 5 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 17, 2011 Page 6 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 17, 2011 Page 7 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 17, 2011 Page 8 of 23
Hopewell MACT ICR Testing Unit No. 2

Emissions Summary

Location: Stack Exit - Method 0011

Compound: Formaldehyde

Average

RunNumber 3 1 2

Mass_mg 0.0106 0.00865 0.00723 0.009

lb/mmBtuO2 3.85E-06 3.11E-06 2.65E-06 0.000

ppm 3.74E-03 2.90E-03 2.50E-03 0.003

ppm@7%O2 3.36E-03 2.71E-03 2.31E-03 0.003

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 1.29E-01 8.72E-02 1.53E-01 0.123

ppm 1.29E+02 8.82E+01 1.60E+02 125.733

ppm@7%O2 1.21E+02 8.16E+01 1.44E+02 115.533

Location: Stack Exit - Method 202

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 4.5 6.8 7.7 6.333

lb/mmBtuO2 1.51E-03 2.27E-03 2.57E-03 0.002

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 1.79E-04 2.09E-03 5.87E-04 0.001

ppm 1.13E-01 1.34E+00 3.88E-01 0.614

ppm@7%O2 1.06E-01 1.24E+00 3.49E-01 0.565

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 149 199 181 176.333

lb/mmBtuO2 3.54E-02 4.68E-02 4.12E-02 0.041

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.79 0.68 0.7 0.723

Thursday, February 17, 2011 Page 9 of 23
Hopewell MACT ICR Testing Unit No. 2

lb/mmBtuO2 1.88E-04 1.60E-04 1.59E-04 0.000

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.000254 0.000404 0.000509 0.000

lb/mmBtuO2 8.58E-08 1.40E-07 1.69E-07 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.001963 0.00211 0.002229 0.002

lb/mmBtuO2 6.63E-07 7.33E-07 7.40E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.000043 0.000041 0.000057 0.000

lb/mmBtuO2 1.45E-08 1.42E-08 1.89E-08 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0001 0.000156 0.000332 0.000

lb/mmBtuO2 3.38E-08 5.42E-08 1.10E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00432 0.00455 0.00449 0.004

lb/mmBtuO2 1.46E-06 1.58E-06 1.49E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.000317 0.000327 0.000422 0.000

lb/mmBtuO2 1.07E-07 1.14E-07 1.40E-07 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.001807 0.002221 0.009816 0.005

lb/mmBtuO2 6.11E-07 7.71E-07 3.26E-06 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.02024 0.002014 0.00318 0.008

lb/mmBtuO2 6.84E-06 6.99E-07 1.06E-06 0.000

Compound: Mercury

Average

Thursday, February 17, 2011 Page 10 of 23
Hopewell MACT ICR Testing Unit No. 2

Process Run Data

RunNumber 1 2 3

Mass_mg 0.0005 0.0005 0.0005 0.001

lb/mmBtuO2 1.69E-07 1.74E-07 1.66E-07 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.002419 0.003399 0.00534 0.004

lb/mmBtuO2 8.18E-07 1.18E-06 1.77E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.000318 0.000386 0.000495 0.000

lb/mmBtuO2 1.07E-07 1.34E-07 1.64E-07 0.000

Location: Stack Exit - Method 5

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 7.8 7.2 6.1 7.033

lb/mmBtuO2 2.61E-03 2.41E-03 2.03E-03 0.002

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 4.94E-01 5.07E-01 4.82E-01 0.494

ppm 2.16E+02 2.24E+02 2.19E+02 219.667

ppm@7%O2 2.02E+02 2.07E+02 1.97E+02 202.000

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 3.54E-01 3.57E-01 3.55E-01 0.355

ppm 2.15E+02 2.20E+02 2.25E+02 220.000

ppm@7%O2 2.01E+02 2.03E+02 2.02E+02 202.000

Thursday, February 17, 2011 Page 11 of 23
Hopewell MACT ICR Testing Unit No. 2

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 637 MMBtu/hr 200

1 Steam Output 487 1,000 lb/hr 0

1 Pressure Drop Across FGD 2.3 in. H2O 0

1 Sorbent Injection Rate 9.7 gal/min 0

1 Unit Gross Electrical Output 43.1 MW 0

1 Unit Net Electrical Output 39.9 MWh 0

2 Heat Input 633 MMBtu/hr 200

2 Steam Output 490 1,000 lb/hr 0

2 Sorbent Injection Rate 8.8 gal/min 0

2 Unit Gross Electrical Output 43.6 MW 0

2 Unit Net Electrical Output 40.5 MWh 0

3 Heat Input 656 MMBtu/hr 200

3 Steam Output 504 1,000 lb/hr 0

3 Sorbent Injection Rate 7.8 gal/min 0

3 Unit Gross Electrical Output 45.7 MW 0

3 Unit Net Electrical Output 41.8 MWh 0

Run Name Value UOM Comments

Target

Value

1 SCRUBBER 90 % 90

2 SCRUBBER 90 % 90

3 SCRUBBER 90 % 90

1 FABRIC FILTER 99.1 % 99.1

2 FABRIC FILTER 99.1 % 99.1

3 FABRIC FILTER 99.1 % 99.1

Run Name Value UOM Comments

1 Fuel Higher Heating Value (wet) 12697 Btu/lb

1 Fuel Higher Heating Value (dry) 13530 Btu/lb

1 Fuel Moisture 6.16 %

1 Fuel Ash Content 8.85 %

1 Fuel Sulfur Content 0.83 %

1 Antimony Content 1 ug/g

Thursday, February 17, 2011 Page 12 of 23
Hopewell MACT ICR Testing Unit No. 2

1 Beryllium Content 2 ug/g

1 Cadmium Content 0.2 ug/g

1 Cobalt Content 8 ug/g

1 Chromium Content 19 ug/g

1 Copper Content 19 ug/g

1 Manganese Content 17 ug/g

1 Nickel Content 15 ug/g

1 Lead Content 9 ug/g

1 Zinc Content 16 ug/g

1 Phosphorus Content 48 ug/g

1 Arsenic Content 6 ug/g

1 Selenium Content 4 ug/g

1 Mercury, Dry Content 0.06 ug/g

2 Fuel Higher Heating Value (wet) 12715 Btu/lb

2 Fuel Higher Heating Value (dry) 13479 Btu/lb

2 Fuel Moisture 5.67 %

2 Fuel Ash Content 9.25 %

2 Fuel Sulfur Content 0.86 %

2 Antimony Content 1 ug/g

2 Beryllium Content 2.1 ug/g

2 Cadmium Content 0.2 ug/g

2 Cobalt Content 8 ug/g

2 Chromium Content 19 ug/g

2 Copper Content 18 ug/g

2 Manganese Content 14 ug/g

2 Nickel Content 15 ug/g

2 Lead Content 7 ug/g

2 Zinc Content 14 ug/g

2 Phosphorus Content 36 ug/g

2 Arsenic Content 5 ug/g

2 Selenium Content 4 ug/g

2 Mercury, Dry Content 0.06 ug/g

3 Fuel Higher Heating Value (wet) 12812 Btu/lb

3 Fuel Higher Heating Value (dry) 13538 Btu/lb

3 Fuel Moisture 5.36 %

3 Fuel Ash Content 8.92 %

3 Fuel Sulfur Content 0.84 %

3 Antimony Content 1 ug/g

3 Beryllium Content 1.9 ug/g

3 Cadmium Content 0.2 ug/g

3 Cobalt Content 8 ug/g

3 Chromium Content 18 ug/g

3 Copper Content 18 ug/g

Thursday, February 17, 2011 Page 13 of 23
Hopewell MACT ICR Testing Unit No. 2

3 Manganese Content 13 ug/g

3 Nickel Content 15 ug/g

3 Lead Content 8 ug/g

3 Zinc Content 15 ug/g

3 Phosphorus Content 43 ug/g

3 Arsenic Content 4 ug/g

3 Selenium Content 3 ug/g

3 Mercury, Dry Content 0.06 ug/g

Thursday, February 17, 2011 Page 14 of 23
Hopewell MACT ICR Testing Unit No. 2

Sampling / Stack Data Results Detail

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 5/6/2010 5/6/2010 5/6/2010

Run Start Time 8:35:00 AM 12:00:00 PM 3:40:00 PM

Run Finish Time 10:44:00 AM 2:13:00 PM 5:51:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.236 0.236 0.236 0.236

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1 1 1 1.000

Barometric Pressure, inches of Mercury 29.85 29.82 29.82 29.830

Average Orifice Meter Differential, inches H2O 1.55 1.49 1.43 1.490

Dry Gas Meter Volume Sampled, cubic feet 87.290 86.238 84.431 85.986

Average Dry Gas Meter Temperature, °F 86.38 96.83 95.83 93.013

Dry Gas Meter Volume Sampled, dscf 84.478 81.799 80.217 82.165

Total Moisture Liquid collected, g 220.7 205 201.2 208.967

Volume of Water Vapor, standard cubic feet 10.39 9.65 9.47 9.837

Moisture Content of Stack Gas, % 10.95 10.55 10.56 10.687

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8905 0.8945 0.8944 0.893

Carbon Dioxide, % 13.34 13.09 13.59 13.340

Oxygen, % 6.05 5.87 5.44 5.787

Carbon Monoxide & Nitrogen, % 80.61 81.04 80.97 80.873

Fuel Factor 1.11 1.15 1.14

Dry Molecular Weight, lb/lb-Mole 30.38 30.33 30.39 30.367

Wet Molecular weight, lb/lb-Mole 29.02 29.03 29.08 29.043

Flue Gas Static Pressure, inches of H2O 0.52 0.52 0.52 0.520

Absolute Flue Gas Pressure, inches of Mercury 29.89 29.86 29.86 29.870

Average Stack Gas Temperature, °F 220.58 228.33 230.25 226.387

Average Velocity Head, inches of H2O 0.6884624838

07553

0.697968156

626783

0.669984722

361286

0.685

Average Stack Gas Velocity, feet/second 52.78 53.46 52.41 52.883

Stack Cross-Sectional Area, square feet 73.391 73.391 73.391 73.391

Dry Volumetric Flow Rate, dry scfm 160,404.5 161,201.4 157,578.1 159,728.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,414.6 235,409.0 230,785.3 232,869.633

Percent Isokinetic of Sampling Rate, % 106.0 102.2 102.5 103.567

Percent Excess Air, % 39.7 37.8 34.1 37.200

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 116 116 116

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Thursday, February 17, 2011 Page 15 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 17, 2011 Page 16 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 202

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 17, 2011 Page 17 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 17, 2011 Page 18 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 17, 2011 Page 19 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 17, 2011 Page 20 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 17, 2011 Page 21 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 17, 2011 Page 22 of 23
Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 17, 2011 Page 23 of 23