### Name: Dana L. Rieves

Title: Compliance Supervisor Company: James River Cogeneration Company Sign Date: Name: Lenny Katerynczuk Title: Project Manager Company: AirNova, Inc. Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date 

## Hopewell MACT ICR Testing Unit No. 2

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 17, 2011 Page 1 of 23

### Hopewell MACT ICR Testing Unit No. 2

Facility Information: James River Cogeneration Company 912 East Randolph Road

Hopewell VA 23860 Contact: Dana L. Rieves
Phone:
Fax:
Email: danarieves@cogentrix.com Testing Company: AirNova, Inc. 5845 Clayton Avenue

Pennsauken NJ 08109 Contact: Lenny Katerynczuk
Phone: 856-486-1500
Fax: 856-486-9896
Email: lenny@airnova.com

Air Permit Number: 50950 Permitted Source ID/Name: James River Cogeneration Company 50950
Permitted Maximum Process Rate: 200 MMBtu/hr (157,500 lbs steam/hr) Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Unit 1 consists of three (3) 200 million Btu heat input per hour bituminous coal-fired Foster Wheeler boilers. Each of the boilers that make up Unit 1 have a dedicated scrubber and bagfilter and are routed to a common turbine stack that is shared by all three boilers. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 5167000055 FRS #: 110000740422

SCC / Description 10100205 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Traveling Grate (Overfeed) Stoker (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Exit 116 960 720 4 116 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 180 0 Stack Exit Formaldehyde Method 0011 3 120 0 Stack Exit Inorganic (Aqueous)

Condensible Part. Method 202 3 120 0 Stack Exit

Organic Condensible

Particulate Method 202 3 120 0 Stack Exit Regulation Description Compound Limit Unit
CAA Section 114 0



### Thursday, February 17, 2011 Page 2 of 23

### Hopewell MACT ICR Testing Unit No. 2

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
None. Total organic compounds

(TOC) as Propane Method 25A 3 180 0 Stack Exit

Hydrogen Fluoride Method 26A 3 180 0 Stack Exit Hydrogen Chloride Method 26A 3 180 0 Stack Exit Nickel Method 29 3 120 0 Stack Exit Arsenic Method 29 3 120 0 Stack Exit Beryllium Method 29 3 120 0 Stack Exit Chromium Method 29 3 120 0 Stack Exit Cadmium Method 29 3 120 0 Stack Exit Mercury Method 29 3 120 0 Stack Exit Manganese Method 29 3 120 0 Stack Exit Cobalt Method 29 3 120 0 Stack Exit Lead Method 29 3 120 0 Stack Exit Antimony Method 29 3 120 0 Stack Exit Selenium Method 29 3 120 0 Stack Exit Filterable Particulate Method 5 3 120 0 Stack Exit Sulfur Dioxide Method 6C 3 180 0 Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0 Stack Exit



### Thursday, February 17, 2011 Page 3 of 23

### Hopewell MACT ICR Testing Unit No. 2

Sampling / Stack Data Results Summary



### Location Stack Exit - Method 0011 Average Run Number 1 2 3
Test Date 5/6/2010 5/6/2010 5/6/2010
Run Start Time 8:35:00 AM 12:00:00 PM 3:40:00 PM

Run Finish Time 10:44:00 AM 2:13:00 PM 5:51:00 PM Net Run Time, minutes 120 120 120 Dry Gas Meter Volume Sampled, dscf 84.478 81.799 80.217 82.165 Moisture Content of Stack Gas, % 10.95 10.55 10.56 10.687 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 13.34 13.09 13.59 13.340 Oxygen, % 6.05 5.87 5.44 5.787 Average Stack Gas Temperature, °F 220.58 228.33 230.25 226.387 Dry Volumetric Flow Rate, dry scfm 160,404.5 161,201.4 157,578.1 159,728.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,414.6 235,409.0 230,785.3 232,869.633 Percent Isokinetic of Sampling Rate, % 106.0 102.2 102.5 103.567 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000
Fw 10640 10640 10640 10,640.000
Fc 1800 1800 1800 1,800.000



### Location Stack Exit - Method 10 Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 17, 2011 Page 4 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 202 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location Stack Exit - Method 25A Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 17, 2011 Page 5 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 26A Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location Stack Exit - Method 29 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 17, 2011 Page 6 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 5 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location Stack Exit - Method 6C Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 17, 2011 Page 7 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 7E Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 17, 2011 Page 8 of 23

### Hopewell MACT ICR Testing Unit No. 2

Emissions Summary



### Location: Stack Exit - Method 0011 Compound: Formaldehyde Average RunNumber 3 1 2 Mass_mg 0.0106 0.00865 0.00723 0.009 lb/mmBtuO2 3.85E-06 3.11E-06 2.65E-06 0.000 ppm 3.74E-03 2.90E-03 2.50E-03 0.003 ppm@7%O2 3.36E-03 2.71E-03 2.31E-03 0.003



### Location: Stack Exit - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 1.29E-01 8.72E-02 1.53E-01 0.123 ppm 1.29E+02 8.82E+01 1.60E+02 125.733 ppm@7%O2 1.21E+02 8.16E+01 1.44E+02 115.533



### Location: Stack Exit - Method 202 Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber 1 2 3 Mass_mg 4.5 6.8 7.7 6.333 lb/mmBtuO2 1.51E-03 2.27E-03 2.57E-03 0.002


### Compound: Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000



### Location: Stack Exit - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.79E-04 2.09E-03 5.87E-04 0.001 ppm 1.13E-01 1.34E+00 3.88E-01 0.614 ppm@7%O2 1.06E-01 1.24E+00 3.49E-01 0.565



### Location: Stack Exit - Method 26A Compound: Hydrogen Chloride Average RunNumber 1 2 3 Mass_mg 149 199 181 176.333 lb/mmBtuO2 3.54E-02 4.68E-02 4.12E-02 0.041


### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 0.79 0.68 0.7 0.723



### Thursday, February 17, 2011 Page 9 of 23

### Hopewell MACT ICR Testing Unit No. 2

lb/mmBtuO2 1.88E-04 1.60E-04 1.59E-04 0.000



### Location: Stack Exit - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.000254 0.000404 0.000509 0.000 lb/mmBtuO2 8.58E-08 1.40E-07 1.69E-07 0.000


### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.001963 0.00211 0.002229 0.002 lb/mmBtuO2 6.63E-07 7.33E-07 7.40E-07 0.000


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.000043 0.000041 0.000057 0.000 lb/mmBtuO2 1.45E-08 1.42E-08 1.89E-08 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.0001 0.000156 0.000332 0.000 lb/mmBtuO2 3.38E-08 5.42E-08 1.10E-07 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.00432 0.00455 0.00449 0.004 lb/mmBtuO2 1.46E-06 1.58E-06 1.49E-06 0.000


### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.000317 0.000327 0.000422 0.000 lb/mmBtuO2 1.07E-07 1.14E-07 1.40E-07 0.000


### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.001807 0.002221 0.009816 0.005 lb/mmBtuO2 6.11E-07 7.71E-07 3.26E-06 0.000


### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.02024 0.002014 0.00318 0.008 lb/mmBtuO2 6.84E-06 6.99E-07 1.06E-06 0.000


### Compound: Mercury Average



### Thursday, February 17, 2011 Page 10 of 23

### Hopewell MACT ICR Testing Unit No. 2

Process Run Data RunNumber 1 2 3 Mass_mg 0.0005 0.0005 0.0005 0.001 lb/mmBtuO2 1.69E-07 1.74E-07 1.66E-07 0.000


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.002419 0.003399 0.00534 0.004 lb/mmBtuO2 8.18E-07 1.18E-06 1.77E-06 0.000


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.000318 0.000386 0.000495 0.000 lb/mmBtuO2 1.07E-07 1.34E-07 1.64E-07 0.000



### Location: Stack Exit - Method 5 Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 7.8 7.2 6.1 7.033 lb/mmBtuO2 2.61E-03 2.41E-03 2.03E-03 0.002



### Location: Stack Exit - Method 6C Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 4.94E-01 5.07E-01 4.82E-01 0.494 ppm 2.16E+02 2.24E+02 2.19E+02 219.667 ppm@7%O2 2.02E+02 2.07E+02 1.97E+02 202.000



### Location: Stack Exit - Method 7E Compound: Nitrogen oxides (NOx) Average Run 1 2 3 lb/mmBtuO2 3.54E-01 3.57E-01 3.55E-01 0.355 ppm 2.15E+02 2.20E+02 2.25E+02 220.000 ppm@7%O2 2.01E+02 2.03E+02 2.02E+02 202.000



### Thursday, February 17, 2011 Page 11 of 23

### Hopewell MACT ICR Testing Unit No. 2

Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 Heat Input 637 MMBtu/hr 200


### 1 Steam Output 487 1,000 lb/hr 0
1 Pressure Drop Across FGD 2.3 in. H2O 0
1 Sorbent Injection Rate 9.7 gal/min 0


### 1 Unit Gross Electrical Output 43.1 MW 0
1 Unit Net Electrical Output 39.9 MWh 0
2 Heat Input 633 MMBtu/hr 200


### 2 Steam Output 490 1,000 lb/hr 0
2 Sorbent Injection Rate 8.8 gal/min 0
2 Unit Gross Electrical Output 43.6 MW 0


### 2 Unit Net Electrical Output 40.5 MWh 0
3 Heat Input 656 MMBtu/hr 200
3 Steam Output 504 1,000 lb/hr 0


### 3 Sorbent Injection Rate 7.8 gal/min 0
3 Unit Gross Electrical Output 45.7 MW 0
3 Unit Net Electrical Output 41.8 MWh 0

Run Name Value UOM Comments Target Value 

### 1 SCRUBBER 90 % 90
2 SCRUBBER 90 % 90


### 3 SCRUBBER 90 % 90
1 FABRIC FILTER 99.1 % 99.1
2 FABRIC FILTER 99.1 % 99.1


### 3 FABRIC FILTER 99.1 % 99.1

Run Name Value UOM Comments 1 Fuel Higher Heating Value (wet) 12697 Btu/lb 1 Fuel Higher Heating Value (dry) 13530 Btu/lb 

### 1 Fuel Moisture 6.16 % 1 Fuel Ash Content 8.85 % 1 Fuel Sulfur Content 0.83 % 1 Antimony Content 1 ug/g



### Thursday, February 17, 2011 Page 12 of 23

### Hopewell MACT ICR Testing Unit No. 2

1 Beryllium Content 2 ug/g 

### 1 Cadmium Content 0.2 ug/g 1 Cobalt Content 8 ug/g 1 Chromium Content 19 ug/g 1 Copper Content 19 ug/g 

### 1 Manganese Content 17 ug/g 1 Nickel Content 15 ug/g 1 Lead Content 9 ug/g 

### 1 Zinc Content 16 ug/g 1 Phosphorus Content 48 ug/g 1 Arsenic Content 6 ug/g 1 Selenium Content 4 ug/g 

### 1 Mercury, Dry Content 0.06 ug/g 2 Fuel Higher Heating Value (wet) 12715 Btu/lb 2 Fuel Higher Heating Value (dry) 13479 Btu/lb 

### 2 Fuel Moisture 5.67 % 2 Fuel Ash Content 9.25 % 2 Fuel Sulfur Content 0.86 % 2 Antimony Content 1 ug/g 

### 2 Beryllium Content 2.1 ug/g 2 Cadmium Content 0.2 ug/g 2 Cobalt Content 8 ug/g 

### 2 Chromium Content 19 ug/g 2 Copper Content 18 ug/g 2 Manganese Content 14 ug/g 2 Nickel Content 15 ug/g 

### 2 Lead Content 7 ug/g 2 Zinc Content 14 ug/g 2 Phosphorus Content 36 ug/g 

### 2 Arsenic Content 5 ug/g 2 Selenium Content 4 ug/g 2 Mercury, Dry Content 0.06 ug/g 3 Fuel Higher Heating Value (wet) 12812 Btu/lb 

### 3 Fuel Higher Heating Value (dry) 13538 Btu/lb 3 Fuel Moisture 5.36 % 3 Fuel Ash Content 8.92 % 

### 3 Fuel Sulfur Content 0.84 % 3 Antimony Content 1 ug/g 3 Beryllium Content 1.9 ug/g 3 Cadmium Content 0.2 ug/g 

### 3 Cobalt Content 8 ug/g 3 Chromium Content 18 ug/g 3 Copper Content 18 ug/g



### Thursday, February 17, 2011 Page 13 of 23

### Hopewell MACT ICR Testing Unit No. 2

3 Manganese Content 13 ug/g 

### 3 Nickel Content 15 ug/g 3 Lead Content 8 ug/g 3 Zinc Content 15 ug/g 3 Phosphorus Content 43 ug/g 

### 3 Arsenic Content 4 ug/g 3 Selenium Content 3 ug/g 3 Mercury, Dry Content 0.06 ug/g



### Thursday, February 17, 2011 Page 14 of 23

### Hopewell MACT ICR Testing Unit No. 2

Sampling / Stack Data Results Detail



### Location Stack Exit - Method 0011 Average Run Number 1 2 3 Test Date 5/6/2010 5/6/2010 5/6/2010 Run Start Time 8:35:00 AM 12:00:00 PM 3:40:00 PM Run Finish Time 10:44:00 AM 2:13:00 PM 5:51:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 120 120 120 Nozzle Diameter, inches 0.236 0.236 0.236 0.236 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1 1 1 1.000 Barometric Pressure, inches of Mercury 29.85 29.82 29.82 29.830 Average Orifice Meter Differential, inches H2O 1.55 1.49 1.43 1.490 Dry Gas Meter Volume Sampled, cubic feet 87.290 86.238 84.431 85.986 Average Dry Gas Meter Temperature, °F 86.38 96.83 95.83 93.013 Dry Gas Meter Volume Sampled, dscf 84.478 81.799 80.217 82.165 Total Moisture Liquid collected, g 220.7 205 201.2 208.967 Volume of Water Vapor, standard cubic feet 10.39 9.65 9.47 9.837 Moisture Content of Stack Gas, % 10.95 10.55 10.56 10.687 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8905 0.8945 0.8944 0.893 Carbon Dioxide, % 13.34 13.09 13.59 13.340 Oxygen, % 6.05 5.87 5.44 5.787 Carbon Monoxide & Nitrogen, % 80.61 81.04 80.97 80.873 Fuel Factor 1.11 1.15 1.14 Dry Molecular Weight, lb/lb-Mole 30.38 30.33 30.39 30.367 Wet Molecular weight, lb/lb-Mole 29.02 29.03 29.08 29.043 Flue Gas Static Pressure, inches of H2O 0.52 0.52 0.52 0.520 Absolute Flue Gas Pressure, inches of Mercury 29.89 29.86 29.86 29.870 Average Stack Gas Temperature, °F 220.58 228.33 230.25 226.387 Average Velocity Head, inches of H2O 0.6884624838 07553 0.697968156

626783 0.669984722

361286 0.685

Average Stack Gas Velocity, feet/second 52.78 53.46 52.41 52.883 Stack Cross-Sectional Area, square feet 73.391 73.391 73.391 73.391 Dry Volumetric Flow Rate, dry scfm 160,404.5 161,201.4 157,578.1 159,728.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,414.6 235,409.0 230,785.3 232,869.633 Percent Isokinetic of Sampling Rate, % 106.0 102.2 102.5 103.567 Percent Excess Air, % 39.7 37.8 34.1 37.200 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Round Duct Diameter, inches 116 116 116 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Thursday, February 17, 2011 Page 15 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 17, 2011 Page 16 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 202 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 17, 2011 Page 17 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 17, 2011 Page 18 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 26A Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 17, 2011 Page 19 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 17, 2011 Page 20 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 5 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 17, 2011 Page 21 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 17, 2011 Page 22 of 23

### Hopewell MACT ICR Testing Unit No. 2

Location Stack Exit - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 17, 2011 Page 23 of 23