SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 1 

## ***PUBLIC NOTICE COPY***

UNITED STATES ENVIRONMENTAL PROTECTION AGENCY Region 4 Atlanta, Georgia

Prevention of Significant Deterioration Permit

For Greenhouse Gas Emissions

Permit PSD

- EPA

- R4013

In accordance with the provisions of the Clean Air Act (CAA), Subchapter I, Part C

, 42 U.S.C. § 7 4 7 0

, and the implementing Prevention of Significant Deterioration (PSD) of Air Quality Regulations at the Code of Federal Regulations (CFR) Title 40 , Section 52.21 (40 CFR § 52.21 ) , and the Federal Implementation Plan at 40 CFR § 52.37 (effective December 30, 2010 and published at 75 FR 82246 (Dec. 30, 2010)) the U

. S

. Environmental Protection Agency Region 4 hereby authorizes :

Shady Hills Power Company, LLC 800 Long Ridge Road Stamford, Connecticut 06927

to construct and operate Greenhouse Gas (GHG) air emissions units as a modification to the existing Sha dy Hills Generating Station located at 14240 Merchant Energy Way within the City

of Spring Hill , in Pasco County, Florida.

T his modification to the Shady Hills facility shall be constructed and operated in accordance with the terms and conditions set forth in this permit.

This p ermit becomes effective on [ INSERT EFFECTIVE DATE]

.

This permit addresses greenhouse gas

- related PSD re quirements, only. For this Project, the State of Florida, through the Florida Department of Environmental Protection, retains jurisdiction over PSD permitting for regulated pollutants other than greenhouse gases. This permit shall not

relieve the owner or operator of the responsi bility to comply fully with all applicable provisions

of federal and state law.

__________ ______________________ Date Signed Carol L. Kemker Acting Director Air, Pesticides, and Toxics Management DivisionSHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 2

AUTHORITY

The EPA issues this permit pursuant to Subchapter I, Part C, of the Clean Air Act (CAA), 42 U.S.C. § 7470, and the implementing PSD Regulations at 40 CFR § 52.21

, and the Federal Implementation Plan at 40 CFR § 52.37 (effective December 30, 2010 and published at 75 FR 82246 (Dec. 30, 2010)) . This permit is based upon application materials submitted to the EPA by Shady Hills Power Company, LLC ( Shady Hills ), dated September 2 5 , 2012, November 30

, 2012, March 27 , 201 3

, and July 26, 2013, supplement al submittals in the administrative record for this permit action, and upon the technical analysis performed by the EPA.

APPLICANT

Shady Hills Power Company, LLC 800 Long Ridge Road Stamford, Connecticut 06927

PROJECT LOCATION

Shady Hills ’s project will be located at the existing Sha dy Hills Generating Station located at 14240 Merchant Energy Way within the City of Spring Hill , in Pasco County, Florida.

PROJECT DESCRIPTION

Shady Hills has applied for a GHG PSD air permit pursuant to the C AA from the EPA Region 4

for the proposed Project. Shady Hills is proposing to build two additional simple cycle

combustion turbine s (Model: G eneral E lectric 7FA.05) at their existing facility . The GE7FA.05 output is 218 megawatts ( MW ) (gross) when firing natural gas and 223 MW (gross) when firing

ultra

- low sulfur distillate (ULSD) fuel oil. The primary fuel will be natural gas with ULSD fuel

oil

, with sulfur content of is 0.015 percent

, as backup fuel. The heat input per turbine would be 2,135 million British thermal units per hour ( MMBtu/hour ) , high heating value (HHV). Ancillary equipment consists of a 2.5 MW emergency generator (EU 007), a natural gas fuel heater (EU 008), a 2.8 million gallon (Mgal) ULSD fuel oil storage tank (EU 00 9), an SF 6 circuit breaker (EU 010), and new on

- site natural gas pipeline.

Shady Hills ’s existing facility consists of three, dual

- fuel, 170 MW (nominal) GE PG7241FA simple cycle combustion turbine (SCCT)

- electrical generators, three 75 feet high exhaust stacks

, and one 2.8 million gallon fuel oil storage tank. The combustion turbine units can operate in simple

- cycle mode and intermittent duty mode. The units are equipped with dry low

- nitrogen oxides ( NO

x ) combustors and water injection capability. The thr ee units are regulated under Phase II of the Federal Acid Rain Program. The existing facility and the Project are located at 14240 Merchant Energy Way within the City of Spring Hill, in Pasco County, Florida. The Project will be located within the existing Shady Hills boundaries. The facility has been in operation since 2002 and operates during peak hours of electrical use

.SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 3

Th is PSD permit for the Project requires the use of Best Available Control Technology (BACT)

to limit emissions of GHG s , to the greatest extent feasible

.

EQUIPMENT LIST

The following devices and activities are subject to this PSD permit:

Unit ID Description

EU 005 223 MW GE 7FA.05 simple cycle combustion turbine

- electrical generator

EU 006 223 MW GE 7FA.05 simple cycle combustion turbine

- electrical generator

EU 007 2,5 00 kilowatt (kW) emergency generator firing ULSD fuel oil

EU 008 10 MMBtu/hr Natural Gas Heater

EU 009 2.8 Mgal Distillate Fuel Oil Storage Tank

EU 010 Three SF 6 Circuit Breaker s Fugitives On

- site pipeline and natural gas supply

PERMIT CONDITIONS

I. PERMIT EXPIRATION

As provided in 40 CFR § 52.21(r), this PSD Permit shall become invalid if construction:

A. is not commenced (as defined in 40 CFR § 52.21(b)(9)) within 18 months after the approval takes effect; or

B. is discontinued for a period of 18 months or more; or

C. is not completed within a reasonable time

.

II. PERMIT NOTIFICATION REQUIREMENTS

Pursuant to Condition IX : SPECIAL CONDITIONS

, Permittee shall notify the EPA Region 4 by letter or electronic mail of the:

A. date construction is commenced, postmarked within 30 days of such date;

B. actual date of initial setting in operation for any purpose, postmarked within 15 days of such date; and

C. date upon which initial certification tests will commence, in accordance with the provisions of Condition IX.E , postmarked not less than 21 days prior to such date. Notification may be provided with the submittal of the certification test protocol required pursuant to Condition IX.E

.SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 4

III. FACILITY OPERATION

A. At all times, including periods of startup, shutdown, shakedown, and malfunction, Permittee shall, to the extent practicable, maintain and operate the facility

, including associated air pollution control equipment

, in a manner consistent with good air pollution control practice s for minimizing emissions

. Determination of whether acceptable operating and maintenance procedures are being used will be based on

infor mation available to the EPA, which may include, but is not limited to, monitoring results, opacity observations, review of operating maintenance procedures and inspection of the facility

.

B. The Permittee shall operate and maintain the CTs and associated components in a manner consistent with good engineering practices for its full utilization.

C. As soon as practicable following initial startup of the CTs (as defined in 40 CFR § 60.2) but prior to commencement of commercial operation (as defined in 40 CFR § 72.2), and thereafter, the Permittee shall develop and implement an operation and maintenance plan for the facility , consistent with Condition III.B above

. At a minimum, the plan shall identify measures for assessing th e performance of the

f acility , the a cceptable range of the plant performance measures for achieving the design electrical output, the methods for monitoring the plant performance measures, and the routine pr ocedures for maintaining the f acility in good operating condition.

IV. MALFUNCTION REPORTING

A. Permittee shall notify the EPA Region 4 via the contact information provided in

Condition X : A GENCY NOTIFICATIONS within two (2) calendar days following the discovery of any failure of air pollution control equipment or process equipment,

or failure of a process to operate in a normal manner, which results in an increase in

emissions above the allowable emission limits stated in Condition I X : S PECIAL

CONDITIONS of this permit.

B. In addition, pursuant to Condition X : A GENCY NOTIFICATIONS

, Permit tee shall provide written notification to the EPA within fifteen (15) calendar days of any such

failure described under Condition IV.A

. This notification shall include a description of the malfunctioning equipment or abnormal operation, the date of the initial malfunction, the period of time over which emissions were increased due to the failure, the cause of the failure, the estimated res ultant emissions in excess of those

allowed in Condition IX : SPECIAL CONDITIONS , and the methods utilized to mitigate emissions and restore normal operations

.

C. Compliance with this malfunction notification provision shall not excuse or otherwise constitute a defense to any violation of this permit or any law or regulation such malfunction may cause.SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 5

V. RIGHT OF ENTRY

The EPA Regional Administrator, and/or an a uthorized representative, upon the presentation of credentials, shall be permitted:

A. t o enter the premises where the f acility is located or where any records are required to be kept under the terms and conditions of this PSD Permit;

B. during normal b usiness hours, to have access to and to copy any records required to be kept under the terms and conditions of this PSD Permit;

C. to inspect any equipment, operation, or method subject to requirements in this PSD Permit; and

D. to sample materials and emissions from the source(s).

VI. TRANSFER OF OWNERSHI P

In the event of any changes in control or ownership of the f acility, this PSD Permit shall be binding on all subsequent owners and operators

. Within 14 days of any such change in

control or ownersh ip, Permittee shall notify the succeeding owner and operator of the existence of this PSD Permit and its conditions by letter

. Permittee shall send a copy of

this letter pursuant to Condition X : A GENCY NOTIFICATIONS to the EPA Region 4 within thirty (30) d ays of its issuance

.

VII. SEVERABILITY

The provisions of this PSD Permit are severable, and, if any provision of the PSD Permit is held invalid, the remainder of this PSD Permit shall not be affected.

VIII. ADHERENCE TO APPLICA TION AND COMPLIANCE WITH OTHER

ENVIRONMENTAL LAWS

A. Permittee shall construct th e P roject in compliance with this PSD permit, the application on which this permit is based

, and all other applicable federal, state, and local air quality regulations. This PSD permit does not release the Permittee from any liability for compliance with other applicable federal, state and local environmental laws and regulations, including the C lean Air Act.

B. If prehistoric or historic artifacts, such as pottery or ceramics, stone tools or metal implements, or any other physical remains that could be associated with Native American cultures, or early colonial or America settlement are encountered at any time within the project site area, the permitted project should cease all activitiesSHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 6 involving subsurface disturbance in the immediate vicinity o f such discoveries. Upon such discovery, P ermittee, or other designee, sh all immediately contact the Fl orida Department of State, Division of Historical Resources, Review and Compliance Section at 850.245.6333 or 800.847.7278, as well as the appropriate permitting agency office s (FDEP and the EPA Region 4) . Project activities sh all not resume
wit hout verbal and/or written auth o r ization from the Division of Historical Resource. In the event that unmarked human remains are encountered during permitted activities, all work shall stop immediately and the proper authorities notified in

accordance with Section 872 .05, Florida Statutes.



### I X. SPECIAL CONDITIONS

A. Air Pollution Control Equipment and Operation

Permittee shall perform any necessary operations to minimize emissions so that emissions are at or below the emission limits specified in this permit

.

B. Combustion Turbine s (EU 005 & 006) Emission Limits

1. Except as noted below under Condition IX.C , on and after the date of initial startup, Permittee shall not discharge or cause the disc harge of emissions from the SC CT Unit s into the atmosphere in excess of the following:

Normal Operation * Emission Limit (per CT) (natural gas firing) ** Emission Limit (per CT ) ( ULSD oil burning ) **

1,377 pounds ( lb ) of carbon dioxide equivalent ( CO 2 e ) per

megawatt

- hour ( MWh ) gross output (12

- month rolling average ) 1, 928 lb CO 2 e /MWh gross

o utput (12

- month rolling average )

* Normal operation is achieved when a CT reaches 50% load or greater.

** Compliance with the above limits shall be demonstrated in accordance with Condition IX.E. 9

.

2. EU 005 and 006 shall not operate an average of more than 3,390 hours per year per CT

on a 12

- month rolling total basis

. No single unit shall operate more than 5,000 hours per

year on a 12

- month rolling total basis, when firing natural gas

. If only on e com bustion turbines is installed, it shall operate no more than 3,390 hours per

year on a 12

- month rolling total basis, when firing natural gas.

Permittee shall monitor and record the number of hours each CT operates monthly and totalled every month for the previous 12 months.

3. EU 005 and 006 shall not operate firing ULSD fuel oil more than 1,0 0 0 combined hours

per year on a 12

- month rolling total . The Permittee shall monitor and record the numberSHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 7

of hours each CT operates on ULSD monthly and totalled every month for the previous

12 months

.

If only one SC CT is installed

, the CT may operate up to 500 hours firing ULSD oil per

year on a 12

- month rolling total

. The single combustion turbine may fire additional 250 hours of ULSD oil, provided that for every hour of ULSD oil fired beyond the 500 hours, the CT mist reduce its capability to fire natural gas by five hours ( i.e., 5:1 natural gas to

ULSD fuel oil ratio).

C. Combustion Turbine s (EU 005 & 006) Startup and Shutdown Emission Limits

1. Startup is defined as the commencement of operation of any emissions unit which has shut down or ceased operation for a period of time sufficient to cause temperature, pressure, chemical, or pollution control device imbalances, which result in excess

emissions above the limits in Condition IX.C

. 3

.

2. Shutdown is the cessation of the operation of an emissions unit for any purpose.

3. Permittee shall not discharge or cause the disc harge of emissions from the CT Unit into the atmosphere in excess of the following during startup and shutdown events :

Startup and

Shutdown Emission Limit (per CT)

(natural gas firing) * Emission Limit (per CT ) ( ULSD oil burning ) *

21 tons CO 2 e per event (12

- month rolling average ) 28 tons CO 2 e per event (12

- month rolling average )

* Compliance with the above limits shall be demonstrated in accordance with Condition IX.E. 9

.

D. Auxiliary Equipment Emission and Operational Limits and Work Practices

1. At all times, the Permittee shall not discharge or cause the discharge of emissions from each unit into the atmosphere in excess of the following , and shall otherwise comply with the following specifications on a 12

- month rollin g total :

Unit ID (description) GHG Limit ( as CO 2 e)

EU 007 Emergency Generator 2,5 00 kW per engine Work Practice

Standards

EU 008 Natural Gas Heater

10 MMBtu/hr 3,965 TPYSHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 8 Unit ID (description) GHG Limit ( as CO 2 e)

EU 010 Circuit Breaker s Three SF 6 Circuit Breakers Work Practice

Standards

2. EU 007 E mergency G enerator shall be properly operated and maintained in accordance to manufacturer’s specifications.

3. The EU 007 Emergency Generator shall be limited to operation of the engine for maintenance and testing purposes, except during an emergency

. Annual hours of operation for emergency stationary reciprocating internal combustion engine (as defined in 40 CFR 63 Subpart ZZZZ) for maintenance and testing, shall not exceed 100 hours per

12

- month rolling total. Permittee shall monitor and re cord the number of hours the emergency generator operates monthly and totalled every month for the previous 12

months.

4. EU 008 Natural Gas H eater shall operate exclusively on natural gas and operate on an efficiency of 75% or higher.

5. EU 010 Circuit B reakers shall be used as electrical interrupters in the event of a power

surge

. EU 010 Circuit Breaker s shall be totally enclosed . Permittee shall install and maintain a leak detection system on the circuit breakers that signals an alarm in the facility’s control room in the event that any circuit breaker looses pressure

. Records of inspection shall be kept in accordance with Condition IX.G

.

6. The on

- site pipeline and natural gas supply system pressure shall be monitored and

record ed continuously against ala rm set points to be determined upon system design and implementation to identify any leaks. Personnel shall treat the natural gas with mercaptan for leak detection by odor. Records of inspection, detected leaks, and repairs (including action taken and duration) shall be kept in accordance with Condition IX.G

.

E. Monitoring and Compliance with GHG Emission Limits for CTs ( EU005 and 006 ) During Normal Operation

1. P er mitt e e sh a ll inst a ll a nd cer ti f y monito r i n g s y st e ms re qui re d f o r qu a nt i f y i n g C O 2

e missions fr om each C T in acc o r d a n ce with the a p pli ca ble re qui r e m e nts of 40 C F R P ar t
75. C onsist e nt with §75

. 4 ( b )

, a ll a ppli ca b l e c e r ti f i ca tion t e sts sh a ll be c o m pl e t e d within

180 ca l e nd a r d a y s a f

t er t he d a te the unit c omm e n ces c omm e r c i a l op e r a tion (a s d ef in e d in

40 C F R 72.2 )

.

2. F ollowing initi a l c e r ti f i ca tion, the C O 2 c ontinuous monitoring s y st e m s h a ll be qu a li t y

a ssu r e d in a c c o r d a n c e with the a ppli ca ble re qui re m e nts of 40 C F R P ar t 75.SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 9

3. The C O 2 c ontinuous monitoring s y st e m sh a ll be ca p a ble of p r od u c i n g hou r l y d e t er min a tions of C O 2 m a ss e missions in tons p e r hour ( tons/h r)

.

4. I n acc o r d a n c e with § 7 5.62, a n initi a l monito r i n g pl a n s h a ll be submitt e d id e nti f y i n g the

m e thodolo g y f

or whi c h C O 2 m a ss e missions wi l l be c ontinuous l y monito r e d. The initi a l

monito r ing pl a n sh a ll be submitt e d no l a t e r th a n 21 d a y s p r ior to the initi a l cer ti f i c a tion

t e sts.

5. P er mitt e e sh a ll p r ovide noti f i ca tions a s sp ec i f

i e d in §75.61 f

or a n y e v e nt re l a t e d to the

c ontinuous m ea su re m e nt of C O 2

.

6. P er mitt e e sh a ll m ea su r e a nd r e c o r d, f o r e ac h C T , the f

ollowing on a n ho u r l y b a sis:

a. Gross e n e rg y output ra t e ( M W ) ;

b. C O 2 m a ss e mission ra t e ( lbs C O 2 /h r) ;

c. H ea t i nput ra te ( MM B t u/h r ; HHV )

, in a cc o r d a n c e with 40 C F R P ar t 75 , Appendix

D ;

d. Unit o p era ti n g t ime a s d e s cr ib e d in §75.57 ( b ) ( 2) ; and

e. The t y

pe ( n a tu r a l g a s or U L S D) and amount of f u e l (gals) b u r n e d

.

7. P er mitt ee sh a ll ca l c u l a te a nd r ec o r d, f or e ac h C T, the f

ollowing on a m onth l y b a sis:

a. Monthly average CO 2 mass emission rate (lbs CO 2 /MWh) calculated as the sum

of each hourly CO 2 mass emission rate times the unit operating time for the hour divided by the sum of the recorded energy output rates time s the unit operation time for the hour for all hours of operation in each month. If more than one fuel is

utilized in a month, a separate average CO 2 emission rate s h all be calculated for

each fuel.

b. Month l y a v e r a g e h ea t ra te ( B tu/k W h) ca l c ul a t e d a s the sum of e a c h hou r l y h e a t input ra te tim e s the unit op era t i ng time f or t h e hour divid e d b y t h e sum of the

r ec o r d e d e n e rg y output ra t e s tim e s the unit op era ting time f or the h our f

or a ll

hou r s of o p e r a tion in eac h month tim e s 1,000. I f m o r e th a n one f

u el is utili z e d in a month, a s e p a r a te a v er a g e h eat input ra te sh a ll be c a l c ul a t ed f or e ach f u e l.

8. P er mitt e e sh a ll ca l c u l a te a nd r ec o r d, f or e ac h C T, the f

ollowing on a n a nnu a l b a sis:

a. The 12

- month r olling a v er a ge C O 2 mass e mission ra te ( lbs C O 2 /M W h) (f or e a c h

f u e l c ombust e d in the p re vio u s 12 months) sh a ll be ca l c ul a t e d a s the sum of ea c h

month l y a v er a ge v a lue tim e s the month l y e n e rg y output ( M W h) divid e d b y the

s u m of the e n e rg y output ( M W h) g e n e ra t e d du r ing the 12 month p e r iod.SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 10 b. The 12

- month r olling a v er a ge h e a t ra te ( B tu/ k W h) (f or e a c h f u e l c ombust e d in the

p re vious 12 months) sh a ll be ca l c ul a t e d a s the s u m of eac h month l y a v e r a g e h ea t

r a te v a lue tim e s the month l y e n e rg y output ( kW h) divid e d b y the sum of t h e

e n e rg y output ( kW h) g e n era t ed du r i n g t he 12 month p er iod

.

9. For demonstrating compliance with the limits specified in Condition IX.B.1 , Permittee shall use the procedures set forth in 40 CFR parts 75 and 98 to determine resulting GHG emissions (as CO 2 e) based on the combination of measured CO 2 emissions and calculated

CO 2 e of other GHG pollutants (as specified in Condition J: GLOBAL WARMING POTENTIAL (GWP ) ). Permitte e shall keep adequate records of these GHG emission

calculations according to requirements in Condition IX.H.1.

F. Monitoring and Compliance with GHG Emission Limits for CTs (EU005 and 006) During Startup and Shutdown

1. Permittee shall monitor and record the time, date, fuel type, and duration of each startup and shutdown event. These records must be kept for five years following the date of such

event.

2. For demonstrating compliance with the limits specified in Condition IX.C.3 , Permittee shall use the procedures set forth in 40 CFR parts 75 and 98 to determine resulting GHG emissions (as CO 2 e) based on the combination of measured CO 2 emissions and calculated

CO 2 e of other GHG pollutants (as specified in Condition J : GLOBAL WARMING POTENTIAL (GWP ) ). Permittee shall keep adequate records o f these GHG emission

calculations according to requirements in Condition IX.H.1.

G. Monitoring and Compliance for Auxiliary Equipment

1. Permittee shall install and maintain an operational non

- resettable totalizing mass or volumetric flow meter in each fuel line to measure fuel use for the 10.0 MMBtu/hr natural gas heater (EU 008) to be recorded monthly and totalled every month for the previous 12 months

.

2. Permittee shall install and maintain an operational non

- resettable elapsed time meter for 2,500 kW emergency use engine ( EU 007) and 10.0 MMBtu/hr Natural gas heater (EU 008) to be recorded monthly and totalled every month for the previous 12 months

.

3. Perm ittee shall calculate and record the operating efficiency of the 10.0 MMBtu/hr natural gas heater (EU 008) on a daily basis.

To maintain the EU 008 operating at a high efficiency, the P ermittee shall perform annual

tune

- ups and meet the associated require ments as follows (i f the unit is not operating on the required date for a tune

- up, the tune

- up must be conducted within one week of

startup ):SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 11 a. I nspect the burner, and clean or replace any components of the burner as necessary (you may delay the burner ins pection until the next scheduled unit shutdown, but you must inspect each burner at least once every 18 months).

b. Inspect the flame pattern, and adjust the burner as necessary to optimize the flame pattern. The adjustment should be consistent with the manufacturer's specifications.

c. Inspect the system controlling the air

- to

- fuel ratio, and ensure that it is correctly calibrated and functioning properly

4. Permittee shall use the annual heat input and data from 40 CFR Part 98, Table C

- 1 to

calculate and re cord CO 2 e emissions from the 10.0 MMBtu/hr natural gas heater (EU 008) using the Global Warming Potential factors as established in Condition J.

5. Permittee shall:

a. Continuously monitor and record circuit breakers pressure;

b. Visually inspect, in accordan ce with manufacturer’s standards, circuit breakers and components on a daily basis;

c. Provide periodic maintenance to the circuit breaks and its components;

d. Repair any leaks and replace equipment as needed;

H. Recordkeeping and Reporting

1. Permittee shall maintain a file of all records, data, measurements, reports, and documents

r elated to the operation of the f acility, including, but not limited to, the following:

a. all records or reports pertaining to adjustments and/or maintenance performed on any system or device at the f

acility;

b. all records relating to performance tests and monitoring of auxiliary combustion equipment ; and

c. all other information that this permit requires Permittee to obtain, maintain, or develop, recorded in a permanent form suitable for inspection.

2. Permittee shall maintain continuous monitoring system records that include the following: the occurrence and duration of any startup, shutdown, shakedown, or malfunction, performance testing, evaluations, calibrations, checks, adjustments

, maintenance, duration of any periods during which a continuous monitoring system or monitoring device is inoperative, and corresponding emission measurements

.SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 12

3. Permittee shall maintain records of all source tests and monitoring and compliance

information required by this permit

.

4. Permittee shall maintain records and submit a written report of all deviations from permit requirements to the EPA semi

- annually, except when: more frequent reporting is specifically required by an applicable subpart; or the Administrator, on a case

- by

- case basis, determines that more frequent reporting is necessary to accurately assess the compliance status of the source

. The report is due on September 30 th and March 31 st and shall include the following:

a. If applicable, t ime intervals, data and magnitude of the excess emissions, the nature and cause (if known), corrective actions taken and preventive measures adopted ;

b. If a pplicable , the time and date of each period during which the continuous monitoring system was inoperative (monitor down

- time), except for zero and span checks, and the nature of continuous monitoring system repairs or adjustments;

c. A statement in the report of a negative declaration; that is, a statement when no

excess emissions occurred or when the continuou s monitoring system has not been inoperative, repaired, or adjusted; ;

d. Any failure to conduct any required source testing, monitoring, or other compliance activities; and

e. Any violation of limitations on operation, including but not limited to restrictions on hours of operation.

5. Excess emissions shall be defi ned as any period in which the f acility emissions exceed the maximum emission limits set forth in this permit.

6. A period of monitor down

- time shall be any unit operating clock hour in which sufficient

data are not obtained by the continuous monitoring system to validate the hour for CO 2

.

7. Excess emissions indicated by continuous monitoring system source testing, or compliance monitoring shall be considered violations of the applicable emission limit for the purpose of this permit.

8. Permittee shall maintain a copy of the current operation and maintenance plan for the

f acility , and shall keep a copy of all prior versions of the plan for a minimum of five

years

. The Permittee shall also keep records of the monitoring data for each of the f acility performance measures and all maintenance activities; the Permittee shall maintain such records for a minimum of five years following the date they are created

9. Unless otherwise specified herein , a ll records required by this PSD Permit shall be retained for not less than five years following the date of such measurements, maintenance, reports , and/or records. These records shall be made available for reviewSHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 13

upon request by the Agency or authorized representative durin g the course of an inspection.

I. Shakedown Periods

The combustion turbine and auxiliary equipment emission limits and requirements in

Conditions I X. B

, I X. C , and I X. D shall not apply during combustion shakedown periods. Shakedown is defined as the period beginning with initial startup and ending no later than initial performance testing, during which the Permittee conducts operational and contractual testing and tuning to ensure the safe, efficient and reliable operation of the plant

. The shakedown period shall not exceed 18 0 days. The requirements of Section III of this permit shall apply at all times.

J. Global Warming Potential (GWP)

For the purposes of showing compli ance with any GHG emission limit in this permit, the

GWP factors listed in 40 CFR Part 98 Subpart A, Table A

- 1 as of the date of this permit

shall be used. The current GWP factors are listed below :

GHG Pollutant GWP Factor

CO 2 1

CH 4 2 1

N 2 O 310

SF 6 23,900

X. A GENCY NOTIFICATIONS

All notifications, reporting or other communications relating to this permit shall be

submitted to:

Chief

Air & EPCRA Enforcement Branch Air, Pesticides and Toxics Management Division U.S. EPA Region 4 61 Forsyth Street, SW Atlanta, GA 30303SHGS Project (PSD

- EPA

- R401 3 )

- Draft PSD Permit 9/1 7 /13 14

In addition, electronic copies of the above

- referenced notifications and communications shall be submitted to the following individuals at their corresponding email address:

Name Email Phone

Jason Dressler dressler.jason@epa.gov 404

- 562

- 9208 Katy R. Lus k y forney.kathleen@epa.gov 404

- 562

- 9 130

Heather Ceron ceron.heather@epa.gov 404

- 562

- 9185