### Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

-down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg+2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

-downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

-down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID

3152 Sunbury

Generation LP 4Control Device Configuraton

Listed (by

boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICRListed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICREIA

Facility Code Facility Name Boiler ID

3152 Sunbury

Generation LP 4

1 8/13/2010 9:27 2 8/13/2010 13:46 3 8/13/2010 18:59 Run Number Test Start Date Test Start TimeMeasured Value (ppm)

8/13/2010 12:49 121.0 8/13/2010 18:11 120.7 8/13/2010 21:59 120.9

Test End Time Test End DateBasis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

Dry U.S. EPA Method 320 ADL Dry U.S. EPA Method 320 ADL Dry U.S. EPA Method 320 ADL CO Emission Test ResultsTest Method Comments lb/mmBtu ppmdv @ 7% O2

0.15 132.8 0.15 133.2 0.15 134.3 Calculated Emission Rate940 1472 7.4 936 1449 7.2 929 1442 7.3 Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%)10.5 8.2 368595 10.4 8.3 367737 10.3 8.4 368102 Flue Gas CO2(%) Flue Gas O2(%) Flue Gas Flow Rate (dscfm)Fuel Input Rate Fuel Type

285.3 1260 bitum inous 287.1 1260 bitum inous 288.9 1260 bitum inous Flue Gas Temperature (F) Fuel #1Units of Measure Measurement Method Fuel Input Rate

ton/day Other 0.234 ton/day Other 0.234 ton/day Other 0.234 Fuel #1Fuel Type Units of Measure Measurement Method

No.2 Fuel Oil (distillate) gallon/m inute Other No.2 Fuel Oil (distillate) gallon/m inute Other No.2 Fuel Oil (distillate) gallon/m inute Other Fuel #2Fuel Input Rate Fuel Type Units of Measure Fuel #3Measurement Method Fuel Input Rate Fuel Type Fuel #4Units of Measure Measurement Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

1 8/13/2010 9:27 8/13/2010 2 8/13/2010 13:46 8/13/2010 3 8/13/2010 18:59 8/13/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) 12:49 0.035 Dry U.S. EPA Method 320 ADL 18:11 0.054 Dry U.S. EPA Method 320 ADL 21:59 0.041 Dry U.S. EPA Method 320 ADL Test End Time Formaldehyde Emission Test ResultsTest Method

Comments lb/mmBtu ppmdv @ 7% O2 The measurement data for formaldehyde has been corrected for sample line bias. The data has been corrected for the line bias by subtracting one half of the ppmv concentration of formaldehyde measured in system zero measurements from the concentration measured in the test run. 4.60E-05 0.039 940 1472 The measurement data for formaldehyde has been corrected for sample line bias. The data has been corrected for the line bias by subtracting one half of the ppmv concentration of formaldehyde measured in system zero measurements from the concentration measured in the test run. 7.00E-05 0.060 936 1449 The measurement data for formaldehyde has been corrected for sample line bias. The data has been corrected for the line bias by subtracting one half of the ppmv concentration of formaldehyde measured in system zero measurements from the concentration measured in the test run. 5.40E-05 0.046 929 1442 Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Calculated Emission RateFuel Input Rate Fuel Type Units of Measure 7.4 10.5 8.2 368595 285.3 1260 bitum inous ton/day 7.2 10.4 8.3 367737 287.1 1260 bitum inous ton/day 7.3 10.3 8.4 368102 288.9 1260 bitum inous ton/day Flue Gas Temperature (F) Fuel #1 Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas Flow

Rate (dscfm)Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Fuel #2 Fuel #3Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

1 8/13/2010 9:27 2 8/13/2010 13:46 3 8/13/2010 18:59 Run Number Test Start Date Test Start TimeMeasured Value (ppm) Basis (Wet or Dry)

8/13/2010 12:49 0.72 Dry 8/13/2010 18:11 0.72 Dry 8/13/2010 21:59 0.72 Dry

Test End Time Test End Date Methane Emission Test ResultsTest Method Used Data Flag (ADL, BDL, DDL) Test Method Comments lb/mmBtu

U.S. EPA Method 320 ADL 5.00E-04 U.S. EPA Method 320 ADL 5.00E-04 U.S. EPA Method 320 ADL 5.00E-04 Methane Emission Test Results Calculated Emission Rateppmdv @ 7% O2

0.79 940 1472 7.4 10.5 8.2 368595 0.79 936 1449 7.2 10.4 8.3 367737 0.80 929 1442 7.3 10.3 8.4 368102 Flue Gas Moisture (%) Flue Gas CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure

285.3 1260 bitum inous ton/day Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute 287.1 1260 bitum inous ton/day Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute 288.9 1260 bitum inous ton/day Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Flue Gas Temperat ure (F) Fuel #1 Fuel #2Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure

Other Other Other Fuel #4 Fuel #3Measurement

Method Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time SO2Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments lb/mmBtu ppmdv @ 7% O2 Calculated Emission Rate Steam Output (1000 lb/hr)Fuel Input Rate Fuel Type Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm) Total Heat Input (mmBtu/hr) Flue Gas Temperature (F) Fuel #1Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Fuel #1 Fuel #2 Fuel #3Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Fuel #3Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

1 8/10/2010 13:00 2 8/11/2010 12:18 3 8/12/2010 10:20 Run Number Test Start Date Test Start TimePlease note QA/QC documentation starting in Column "AI"

Measured Value (μg/dscm) Basis (Wet or Dry)

8/10/2010 15:40 2.6644 Dry 8/11/2010 15:15 3.4302 Dry 8/12/2010 14:25 2.3088 Dry Test End Date Test End Time Total Vapor Phase Mercury Emission Test ResultsPlease note QA/QC documentation starting in Column "AI"

Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments (lb/mmBtu)

U.S. EPA Method 30B ADL 2.80E-06 953 U.S. EPA Method 30B ADL 3.52E-06 963 U.S. EPA Method 30B ADL 2.37E-06 944 Steam Output (1000 lb/hr) Total Vapor Phase Mercury Emission Test ResultsFuel Input Rate

1470 8.15 291.75 1156 1451 8.07 295.33 1438 1437 8.11 286.31 1346 Flue Gas Temperature (F) Total Heat Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm)Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate

bitum inous ton/day Other bitum inous ton/day Other bitum inous ton/day Other Fuel #1 Fuel #2Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #3 Fuel #4QA /QC Documentation

Trap ID Section 1

Mass (ng) Section 2

Mass (ng) Total

Mass (ng) Initial

Spike (ng) Total NonSpike (ng)

78009 268.74 0.00 268.74 0.0 268.74 78093 272.20 1.26 273.46 0.0 273.46 78112 191.46 1.44 192.90 0.0 192.90 Other Supporting InformationSample

Volume (dsL) Volume

Difference (%) Volume Diff. Limit Breaktrough

(%) Breaktrough

Limit Concentration

(μg/dscm) Trap ID

92.18 7.91 0.00 2.9154 74825 80.33 5.96 0.46 3.4042 74852 83.75 1.96 0.75 2.3033 78034 Trap #1

≤20% of field

recovery test ≤ 10% of Section 1 Hg

mass for Hg conc. >1 μg/dscm: or ≤ 20% of Section 1 for Hg conc. ≤1 μg/dscmSection 1

Mass Section 2

Mass Total

Mass Initial

Spike Total NonSpike Sample

Volume Volume

Difference (%) Volume Diff. Limit

519.03 4.34 523.37 300 223.37 92.55 8.35 574.39 2.64 577.03 300 277.03 80.16 6.16 493.66 1.08 494.74 300 194.74 84.15 1.49 Trap #2

≤20% of field

recovery testBreaktrough (%) Breaktrough Limit Concentration

(μg/dscm) Abs. diff. RD (%) Limit C rec

0.84 2.4135 0.501877 9.42 2.693 0.46 3.4560 0.051755 0.75 3.777 0.22 2.3142 0.010917 0.24 3.580 Paired Trap Agreement (RD) Measured Spike Recovery ( R )

≤ 10% of Section 1 Hg mass for Hg conc. >1 μg/dscm: or ≤ 20% of Section 1 for Hg conc. ≤1 μg/dscm ≥10 % RD mass for Hg conc. >1 μg/dscm: or ≤20% RD or ≤0.2 μg/dscm abs.diff. for Hg conc. ≤1 μg/dscmR (%) by

Run Ravg(%) Limit

83.07 100.92 100.43 Average Recovery

, between 85 and 115% Measured Spike Recovery ( R )

94.8EIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

Run Number Test Start Date Test Start TimeMeasured Hg 0Value (μg/dscm) Measured Hg +2Value (μg/dscm) Test End Time Test End DateMeasured Hg PValue

(μg/dscm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Total Vapor Phase Mercury Emission Test ResultsTest Method

Comments Total Mercury (lb/mmBtu) Steam Output

(1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel #1 Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Other Supporting Information Fuel #4EIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

Speciated Volatile Organic HAP Emission Data

Methyl chloride 1 8/13/2010 Methyl chloride 1 8/13/2010 Methyl chloride 1 8/13/2010 Methyl chloride 2 8/13/2010 Methyl chloride 2 8/13/2010 Methyl chloride 2 8/13/2010 Methyl chloride 3 8/13/2010 Methyl chloride 3 8/13/2010 Methyl chloride 3 8/13/2010 Vinyl chloride (chloroethene) 1 8/13/2010 Vinyl chloride (chloroethene) 1 8/13/2010 Vinyl chloride (chloroethene) 1 8/13/2010 Vinyl chloride (chloroethene) 2 8/13/2010 Vinyl chloride (chloroethene) 2 8/13/2010 Vinyl chloride (chloroethene) 2 8/13/2010 Vinyl chloride (chloroethene) 3 8/13/2010 Vinyl chloride (chloroethene) 3 8/13/2010 Vinyl chloride (chloroethene) 3 8/13/2010 Methyl bromide 1 8/13/2010 Methyl bromide 1 8/13/2010 Methyl bromide 1 8/13/2010 Methyl bromide 2 8/13/2010 Methyl bromide 2 8/13/2010 Methyl bromide 2 8/13/2010 Methyl bromide 3 8/13/2010 Methyl bromide 3 8/13/2010 Methyl bromide 3 8/13/2010 Ethyl chloride 1 8/13/2010 Ethyl chloride 1 8/13/2010 Ethyl chloride 1 8/13/2010 Ethyl chloride 2 8/13/2010 Ethyl chloride 2 8/13/2010 Ethyl chloride 2 8/13/2010 Ethyl chloride 3 8/13/2010 Ethyl chloride 3 8/13/2010 Ethyl chloride 3 8/13/2010 Carbon disulfide 1 8/13/2010 Carbon disulfide 1 8/13/2010 Carbon disulfide 1 8/13/2010 Carbon disulfide 2 8/13/2010 Carbon disulfide 2 8/13/2010 Carbon disulfide 2 8/13/2010 Carbon disulfide 3 8/13/2010

Compound (use drop down to define for as many rows as

needed) Run Number Test Start DateCarbon disulfide 3 8/13/2010

Carbon disulfide 3 8/13/2010 Vinylidene chloride 1 8/13/2010 Vinylidene chloride 1 8/13/2010 Vinylidene chloride 1 8/13/2010 Vinylidene chloride 2 8/13/2010 Vinylidene chloride 2 8/13/2010 Vinylidene chloride 2 8/13/2010 Vinylidene chloride 3 8/13/2010 Vinylidene chloride 3 8/13/2010 Vinylidene chloride 3 8/13/2010 Methylene chloride 1 8/13/2010 Methylene chloride 1 8/13/2010 Methylene chloride 1 8/13/2010 Methylene chloride 2 8/13/2010 Methylene chloride 2 8/13/2010 Methylene chloride 2 8/13/2010 Methylene chloride 3 8/13/2010 Methylene chloride 3 8/13/2010 Methylene chloride 3 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 1 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 1 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 1 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 2 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 2 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 2 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 3 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 3 8/13/2010 Ethylidene dichloride (1,1-dichloroethane) 3 8/13/2010 Methyl ethyl ketone (2-butanone) 1 8/13/2010 Methyl ethyl ketone (2-butanone) 1 8/13/2010 Methyl ethyl ketone (2-butanone) 1 8/13/2010 Methyl ethyl ketone (2-butanone) 2 8/13/2010 Methyl ethyl ketone (2-butanone) 2 8/13/2010 Methyl ethyl ketone (2-butanone) 2 8/13/2010 Methyl ethyl ketone (2-butanone) 3 8/13/2010 Methyl ethyl ketone (2-butanone) 3 8/13/2010 Methyl ethyl ketone (2-butanone) 3 8/13/2010 Chloroform 1 8/13/2010 Chloroform 1 8/13/2010 Chloroform 1 8/13/2010 Chloroform 2 8/13/2010 Chloroform 2 8/13/2010 Chloroform 2 8/13/2010 Chloroform 3 8/13/2010 Chloroform 3 8/13/2010 Chloroform 3 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 1 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 1 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 1 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 2 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 2 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 2 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 3 8/13/2010 Methyl chloroform (1,1,1-trichloroethane) 3 8/13/2010Methyl chloroform (1,1,1-trichloroethane) 3 8/13/2010

Carbon tetrachloride 1 8/13/2010 Carbon tetrachloride 1 8/13/2010 Carbon tetrachloride 1 8/13/2010 Carbon tetrachloride 2 8/13/2010 Carbon tetrachloride 2 8/13/2010 Carbon tetrachloride 2 8/13/2010 Carbon tetrachloride 3 8/13/2010 Carbon tetrachloride 3 8/13/2010 Carbon tetrachloride 3 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 1 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 1 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 1 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 2 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 2 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 2 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 3 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 3 8/13/2010 Ethylene dichloride (1,2-dichloroethane) 3 8/13/2010 Benzene 1 8/13/2010 Benzene 1 8/13/2010 Benzene 1 8/13/2010 Benzene 2 8/13/2010 Benzene 2 8/13/2010 Benzene 2 8/13/2010 Benzene 3 8/13/2010 Benzene 3 8/13/2010 Benzene 3 8/13/2010 Trichloroethylene 1 8/13/2010 Trichloroethylene 1 8/13/2010 Trichloroethylene 1 8/13/2010 Trichloroethylene 2 8/13/2010 Trichloroethylene 2 8/13/2010 Trichloroethylene 2 8/13/2010 Trichloroethylene 3 8/13/2010 Trichloroethylene 3 8/13/2010 Trichloroethylene 3 8/13/2010 Propylene dichloride (1,2-dichloropropane) 1 8/13/2010 Propylene dichloride (1,2-dichloropropane) 1 8/13/2010 Propylene dichloride (1,2-dichloropropane) 1 8/13/2010 Propylene dichloride (1,2-dichloropropane) 2 8/13/2010 Propylene dichloride (1,2-dichloropropane) 2 8/13/2010 Propylene dichloride (1,2-dichloropropane) 2 8/13/2010 Propylene dichloride (1,2-dichloropropane) 3 8/13/2010 Propylene dichloride (1,2-dichloropropane) 3 8/13/2010 Propylene dichloride (1,2-dichloropropane) 3 8/13/2010 cis-1,3-Dichloropropene 1 8/13/2010 cis-1,3-Dichloropropene 1 8/13/2010 cis-1,3-Dichloropropene 1 8/13/2010 cis-1,3-Dichloropropene 2 8/13/2010 cis-1,3-Dichloropropene 2 8/13/2010 cis-1,3-Dichloropropene 2 8/13/2010 cis-1,3-Dichloropropene 3 8/13/2010 cis-1,3-Dichloropropene 3 8/13/2010 cis-1,3-Dichloropropene 3 8/13/2010Methyl isobutyl ketone (hexone) 1 8/13/2010

Methyl isobutyl ketone (hexone) 1 8/13/2010 Methyl isobutyl ketone (hexone) 1 8/13/2010 Methyl isobutyl ketone (hexone) 2 8/13/2010 Methyl isobutyl ketone (hexone) 2 8/13/2010 Methyl isobutyl ketone (hexone) 2 8/13/2010 Methyl isobutyl ketone (hexone) 3 8/13/2010 Methyl isobutyl ketone (hexone) 3 8/13/2010 Methyl isobutyl ketone (hexone) 3 8/13/2010 1,1,2-Trichloroethane 1 8/13/2010 1,1,2-Trichloroethane 1 8/13/2010 1,1,2-Trichloroethane 1 8/13/2010 1,1,2-Trichloroethane 2 8/13/2010 1,1,2-Trichloroethane 2 8/13/2010 1,1,2-Trichloroethane 2 8/13/2010 1,1,2-Trichloroethane 3 8/13/2010 1,1,2-Trichloroethane 3 8/13/2010 1,1,2-Trichloroethane 3 8/13/2010 Toluene 1 8/13/2010 Toluene 1 8/13/2010 Toluene 1 8/13/2010 Toluene 2 8/13/2010 Toluene 2 8/13/2010 Toluene 2 8/13/2010 Toluene 3 8/13/2010 Toluene 3 8/13/2010 Toluene 3 8/13/2010 Tetrachloroethylene 1 8/13/2010 Tetrachloroethylene 1 8/13/2010 Tetrachloroethylene 1 8/13/2010 Tetrachloroethylene 2 8/13/2010 Tetrachloroethylene 2 8/13/2010 Tetrachloroethylene 2 8/13/2010 Tetrachloroethylene 3 8/13/2010 Tetrachloroethylene 3 8/13/2010 Tetrachloroethylene 3 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 1 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 1 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 1 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 2 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 2 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 2 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 3 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 3 8/13/2010 Ethylene dibrom ide (1,2-dibromoethane) 3 8/13/2010 Chlorobenzene 1 8/13/2010 Chlorobenzene 1 8/13/2010 Chlorobenzene 1 8/13/2010 Chlorobenzene 2 8/13/2010 Chlorobenzene 2 8/13/2010 Chlorobenzene 2 8/13/2010 Chlorobenzene 3 8/13/2010 Chlorobenzene 3 8/13/2010 Chlorobenzene 3 8/13/2010 Ethylbenzene 1 8/13/2010Ethylbenzene 1 8/13/2010

Ethylbenzene 1 8/13/2010 Ethylbenzene 2 8/13/2010 Ethylbenzene 2 8/13/2010 Ethylbenzene 2 8/13/2010 Ethylbenzene 3 8/13/2010 Ethylbenzene 3 8/13/2010 Ethylbenzene 3 8/13/2010 Xylenes (isomer & mixtures) 1 8/13/2010 Xylenes (isomer & mixtures) 1 8/13/2010 Xylenes (isomer & mixtures) 1 8/13/2010 Xylenes (isomer & mixtures) 2 8/13/2010 Xylenes (isomer & mixtures) 2 8/13/2010 Xylenes (isomer & mixtures) 2 8/13/2010 Xylenes (isomer & mixtures) 3 8/13/2010 Xylenes (isomer & mixtures) 3 8/13/2010 Xylenes (isomer & mixtures) 3 8/13/2010 o-Xylene 1 8/13/2010 o-Xylene 1 8/13/2010 o-Xylene 1 8/13/2010 o-Xylene 2 8/13/2010 o-Xylene 2 8/13/2010 o-Xylene 2 8/13/2010 o-Xylene 3 8/13/2010 o-Xylene 3 8/13/2010 o-Xylene 3 8/13/2010 Styrene 1 8/13/2010 Styrene 1 8/13/2010 Styrene 1 8/13/2010 Styrene 2 8/13/2010 Styrene 2 8/13/2010 Styrene 2 8/13/2010 Styrene 3 8/13/2010 Styrene 3 8/13/2010 Styrene 3 8/13/2010 Bromoform (tribromomethane) 1 8/13/2010 Bromoform (tribromomethane) 1 8/13/2010 Bromoform (tribromomethane) 1 8/13/2010 Bromoform (tribromomethane) 2 8/13/2010 Bromoform (tribromomethane) 2 8/13/2010 Bromoform (tribromomethane) 2 8/13/2010 Bromoform (tribromomethane) 3 8/13/2010 Bromoform (tribromomethane) 3 8/13/2010 Bromoform (tribromomethane) 3 8/13/2010 1, 1, 2, 2-Tetrachloroethane 1 8/13/2010 1, 1, 2, 2-Tetrachloroethane 1 8/13/2010 1, 1, 2, 2-Tetrachloroethane 1 8/13/2010 1, 1, 2, 2-Tetrachloroethane 2 8/13/2010 1, 1, 2, 2-Tetrachloroethane 2 8/13/2010 1, 1, 2, 2-Tetrachloroethane 2 8/13/2010 1, 1, 2, 2-Tetrachloroethane 3 8/13/2010 1, 1, 2, 2-Tetrachloroethane 3 8/13/2010 1, 1, 2, 2-Tetrachloroethane 3 8/13/2010 Acetone 1 8/13/2010 Acetone 1 8/13/2010Acetone 1 8/13/2010

Acetone 2 8/13/2010 Acetone 2 8/13/2010 Acetone 2 8/13/2010 Acetone 3 8/13/2010 Acetone 3 8/13/2010 Acetone 3 8/13/2010 Bromobenzene 1 8/13/2010 Bromobenzene 1 8/13/2010 Bromobenzene 1 8/13/2010 Bromobenzene 2 8/13/2010 Bromobenzene 2 8/13/2010 Bromobenzene 2 8/13/2010 Bromobenzene 3 8/13/2010 Bromobenzene 3 8/13/2010 Bromobenzene 3 8/13/2010 Bromochloromethane 1 8/13/2010 Bromochloromethane 1 8/13/2010 Bromochloromethane 1 8/13/2010 Bromochloromethane 2 8/13/2010 Bromochloromethane 2 8/13/2010 Bromochloromethane 2 8/13/2010 Bromochloromethane 3 8/13/2010 Bromochloromethane 3 8/13/2010 Bromochloromethane 3 8/13/2010 Bromodichloromethane 1 8/13/2010 Bromodichloromethane 1 8/13/2010 Bromodichloromethane 1 8/13/2010 Bromodichloromethane 2 8/13/2010 Bromodichloromethane 2 8/13/2010 Bromodichloromethane 2 8/13/2010 Bromodichloromethane 3 8/13/2010 Bromodichloromethane 3 8/13/2010 Bromodichloromethane 3 8/13/2010 n-Butylbenzene 1 8/13/2010 n-Butylbenzene 1 8/13/2010 n-Butylbenzene 1 8/13/2010 n-Butylbenzene 2 8/13/2010 n-Butylbenzene 2 8/13/2010 n-Butylbenzene 2 8/13/2010 n-Butylbenzene 3 8/13/2010 n-Butylbenzene 3 8/13/2010 n-Butylbenzene 3 8/13/2010 sec-Butylbenzene 1 8/13/2010 sec-Butylbenzene 1 8/13/2010 sec-Butylbenzene 1 8/13/2010 sec-Butylbenzene 2 8/13/2010 sec-Butylbenzene 2 8/13/2010 sec-Butylbenzene 2 8/13/2010 sec-Butylbenzene 3 8/13/2010 sec-Butylbenzene 3 8/13/2010 sec-Butylbenzene 3 8/13/2010 tert-Butylbenzene 1 8/13/2010 tert-Butylbenzene 1 8/13/2010 tert-Butylbenzene 1 8/13/2010tert-Butylbenzene 2 8/13/2010

tert-Butylbenzene 2 8/13/2010 tert-Butylbenzene 2 8/13/2010 tert-Butylbenzene 3 8/13/2010 tert-Butylbenzene 3 8/13/2010 tert-Butylbenzene 3 8/13/2010 Chlorodibromomethane 1 8/13/2010 Chlorodibromomethane 1 8/13/2010 Chlorodibromomethane 1 8/13/2010 Chlorodibromomethane 2 8/13/2010 Chlorodibromomethane 2 8/13/2010 Chlorodibromomethane 2 8/13/2010 Chlorodibromomethane 3 8/13/2010 Chlorodibromomethane 3 8/13/2010 Chlorodibromomethane 3 8/13/2010 2-Chlorotoluene 1 8/13/2010 2-Chlorotoluene 1 8/13/2010 2-Chlorotoluene 1 8/13/2010 2-Chlorotoluene 2 8/13/2010 2-Chlorotoluene 2 8/13/2010 2-Chlorotoluene 2 8/13/2010 2-Chlorotoluene 3 8/13/2010 2-Chlorotoluene 3 8/13/2010 2-Chlorotoluene 3 8/13/2010 4-Chlorotoluene 1 8/13/2010 4-Chlorotoluene 1 8/13/2010 4-Chlorotoluene 1 8/13/2010 4-Chlorotoluene 2 8/13/2010 4-Chlorotoluene 2 8/13/2010 4-Chlorotoluene 2 8/13/2010 4-Chlorotoluene 3 8/13/2010 4-Chlorotoluene 3 8/13/2010 4-Chlorotoluene 3 8/13/2010 1,2-Dibromo-3-chloropropane 1 8/13/2010 1,2-Dibromo-3-chloropropane 1 8/13/2010 1,2-Dibromo-3-chloropropane 1 8/13/2010 1,2-Dibromo-3-chloropropane 2 8/13/2010 1,2-Dibromo-3-chloropropane 2 8/13/2010 1,2-Dibromo-3-chloropropane 2 8/13/2010 1,2-Dibromo-3-chloropropane 3 8/13/2010 1,2-Dibromo-3-chloropropane 3 8/13/2010 1,2-Dibromo-3-chloropropane 3 8/13/2010 Dibromomethane 1 8/13/2010 Dibromomethane 1 8/13/2010 Dibromomethane 1 8/13/2010 Dibromomethane 2 8/13/2010 Dibromomethane 2 8/13/2010 Dibromomethane 2 8/13/2010 Dibromomethane 3 8/13/2010 Dibromomethane 3 8/13/2010 Dibromomethane 3 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 2 8/13/20101,2-Dichlorobenzene 2 8/13/2010

1,2-Dichlorobenzene 2 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 Dichlorodifluoromethane 1 8/13/2010 Dichlorodifluoromethane 1 8/13/2010 Dichlorodifluoromethane 1 8/13/2010 Dichlorodifluoromethane 2 8/13/2010 Dichlorodifluoromethane 2 8/13/2010 Dichlorodifluoromethane 2 8/13/2010 Dichlorodifluoromethane 3 8/13/2010 Dichlorodifluoromethane 3 8/13/2010 Dichlorodifluoromethane 3 8/13/2010 cis-1,2-Dichloroethene 1 8/13/2010 cis-1,2-Dichloroethene 1 8/13/2010 cis-1,2-Dichloroethene 1 8/13/2010 cis-1,2-Dichloroethene 2 8/13/2010 cis-1,2-Dichloroethene 2 8/13/2010 cis-1,2-Dichloroethene 2 8/13/2010 cis-1,2-Dichloroethene 3 8/13/2010 cis-1,2-Dichloroethene 3 8/13/2010 cis-1,2-Dichloroethene 3 8/13/2010 trans-1,2-Dichloroethene 1 8/13/2010 trans-1,2-Dichloroethene 1 8/13/2010 trans-1,2-Dichloroethene 1 8/13/2010 trans-1,2-Dichloroethene 2 8/13/2010 trans-1,2-Dichloroethene 2 8/13/2010 trans-1,2-Dichloroethene 2 8/13/2010 trans-1,2-Dichloroethene 3 8/13/2010 trans-1,2-Dichloroethene 3 8/13/2010 trans-1,2-Dichloroethene 3 8/13/2010 1,2-Dichloropropane 1 8/13/2010 1,2-Dichloropropane 1 8/13/2010 1,2-Dichloropropane 1 8/13/2010 1,2-Dichloropropane 2 8/13/2010 1,2-Dichloropropane 2 8/13/20101,2-Dichloropropane 2 8/13/2010

1,2-Dichloropropane 3 8/13/2010 1,2-Dichloropropane 3 8/13/2010 1,2-Dichloropropane 3 8/13/2010 1,3-Dichloropropane 1 8/13/2010 1,3-Dichloropropane 1 8/13/2010 1,3-Dichloropropane 1 8/13/2010 1,3-Dichloropropane 2 8/13/2010 1,3-Dichloropropane 2 8/13/2010 1,3-Dichloropropane 2 8/13/2010 1,3-Dichloropropane 3 8/13/2010 1,3-Dichloropropane 3 8/13/2010 1,3-Dichloropropane 3 8/13/2010 2,2-Dichloropropane 1 8/13/2010 2,2-Dichloropropane 1 8/13/2010 2,2-Dichloropropane 1 8/13/2010 2,2-Dichloropropane 2 8/13/2010 2,2-Dichloropropane 2 8/13/2010 2,2-Dichloropropane 2 8/13/2010 2,2-Dichloropropane 3 8/13/2010 2,2-Dichloropropane 3 8/13/2010 2,2-Dichloropropane 3 8/13/2010 trans-1,3-Dichloropropene 1 8/13/2010 trans-1,3-Dichloropropene 1 8/13/2010 trans-1,3-Dichloropropene 1 8/13/2010 trans-1,3-Dichloropropene 2 8/13/2010 trans-1,3-Dichloropropene 2 8/13/2010 trans-1,3-Dichloropropene 2 8/13/2010 trans-1,3-Dichloropropene 3 8/13/2010 trans-1,3-Dichloropropene 3 8/13/2010 trans-1,3-Dichloropropene 3 8/13/2010 1,1-Dichloropropene 1 8/13/2010 1,1-Dichloropropene 1 8/13/2010 1,1-Dichloropropene 1 8/13/2010 1,1-Dichloropropene 2 8/13/2010 1,1-Dichloropropene 2 8/13/2010 1,1-Dichloropropene 2 8/13/2010 1,1-Dichloropropene 3 8/13/2010 1,1-Dichloropropene 3 8/13/2010 1,1-Dichloropropene 3 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 3 8/13/2010 Hexachlorobutadiene 3 8/13/2010 Hexachlorobutadiene 3 8/13/2010 2-Hexanone 1 8/13/2010 2-Hexanone 1 8/13/2010 2-Hexanone 1 8/13/2010 2-Hexanone 2 8/13/2010 2-Hexanone 2 8/13/2010 2-Hexanone 2 8/13/20102-Hexanone 3 8/13/2010

2-Hexanone 3 8/13/2010 2-Hexanone 3 8/13/2010 Isopropylbenzene 1 8/13/2010 Isopropylbenzene 1 8/13/2010 Isopropylbenzene 1 8/13/2010 Isopropylbenzene 2 8/13/2010 Isopropylbenzene 2 8/13/2010 Isopropylbenzene 2 8/13/2010 Isopropylbenzene 3 8/13/2010 Isopropylbenzene 3 8/13/2010 Isopropylbenzene 3 8/13/2010 p-Isopropyltoluene 1 8/13/2010 p-Isopropyltoluene 1 8/13/2010 p-Isopropyltoluene 1 8/13/2010 p-Isopropyltoluene 2 8/13/2010 p-Isopropyltoluene 2 8/13/2010 p-Isopropyltoluene 2 8/13/2010 p-Isopropyltoluene 3 8/13/2010 p-Isopropyltoluene 3 8/13/2010 p-Isopropyltoluene 3 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 3 8/13/2010 Naphthalene 3 8/13/2010 Naphthalene 3 8/13/2010 n-Propylbenzene 1 8/13/2010 n-Propylbenzene 1 8/13/2010 n-Propylbenzene 1 8/13/2010 n-Propylbenzene 2 8/13/2010 n-Propylbenzene 2 8/13/2010 n-Propylbenzene 2 8/13/2010 n-Propylbenzene 3 8/13/2010 n-Propylbenzene 3 8/13/2010 n-Propylbenzene 3 8/13/2010 1,1,1,2-Tetrachloroethane 1 8/13/2010 1,1,1,2-Tetrachloroethane 1 8/13/2010 1,1,1,2-Tetrachloroethane 1 8/13/2010 1,1,1,2-Tetrachloroethane 2 8/13/2010 1,1,1,2-Tetrachloroethane 2 8/13/2010 1,1,1,2-Tetrachloroethane 2 8/13/2010 1,1,1,2-Tetrachloroethane 3 8/13/2010 1,1,1,2-Tetrachloroethane 3 8/13/2010 1,1,1,2-Tetrachloroethane 3 8/13/2010 1,2,3-Trichlorobenzene 1 8/13/2010 1,2,3-Trichlorobenzene 1 8/13/2010 1,2,3-Trichlorobenzene 1 8/13/2010 1,2,3-Trichlorobenzene 2 8/13/2010 1,2,3-Trichlorobenzene 2 8/13/2010 1,2,3-Trichlorobenzene 2 8/13/2010 1,2,3-Trichlorobenzene 3 8/13/20101,2,3-Trichlorobenzene 3 8/13/2010

1,2,3-Trichlorobenzene 3 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 Trichlorofluoromethane 1 8/13/2010 Trichlorofluoromethane 1 8/13/2010 Trichlorofluoromethane 1 8/13/2010 Trichlorofluoromethane 2 8/13/2010 Trichlorofluoromethane 2 8/13/2010 Trichlorofluoromethane 2 8/13/2010 Trichlorofluoromethane 3 8/13/2010 Trichlorofluoromethane 3 8/13/2010 Trichlorofluoromethane 3 8/13/2010 1,2,4-Trimethylbenzene 1 8/13/2010 1,2,4-Trimethylbenzene 1 8/13/2010 1,2,4-Trimethylbenzene 1 8/13/2010 1,2,4-Trimethylbenzene 2 8/13/2010 1,2,4-Trimethylbenzene 2 8/13/2010 1,2,4-Trimethylbenzene 2 8/13/2010 1,2,4-Trimethylbenzene 3 8/13/2010 1,2,4-Trimethylbenzene 3 8/13/2010 1,2,4-Trimethylbenzene 3 8/13/2010 1,3,5-Trimethylbenzene 1 8/13/2010 1,3,5-Trimethylbenzene 1 8/13/2010 1,3,5-Trimethylbenzene 1 8/13/2010 1,3,5-Trimethylbenzene 2 8/13/2010 1,3,5-Trimethylbenzene 2 8/13/2010 1,3,5-Trimethylbenzene 2 8/13/2010 1,3,5-Trimethylbenzene 3 8/13/2010 1,3,5-Trimethylbenzene 3 8/13/2010 1,3,5-Trimethylbenzene 3 8/13/2010Note: Each run should include a value for each fraction and the total for each pollutant.

Fraction

9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* Test Start Time Test End Date Test End Time18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half**18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half*9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half**9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half*15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half**15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half*18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 Total 9:30 8/13/2010 13:35 Front Half* 9:30 8/13/2010 13:35 Back Half** 9:30 8/13/2010 13:35 Total 15:05 8/13/2010 17:48 Front Half* 15:05 8/13/2010 17:48 Back Half** 15:05 8/13/2010 17:48 Total 18:05 8/13/2010 20:48 Front Half* 18:05 8/13/2010 20:48 Back Half** 18:05 8/13/2010 20:48 TotalFootnotes:

* Front half fraction contains filter, cyclone, and cartridge ** Back half fraction contains condensate, solvent, impingers

Measured Value (μg/m3) Basis Test Method Used [<13.40] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 6.46 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<19.87] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 7.35 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<22.49] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<29.84] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.30] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 10.65 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<15.95] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.92] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.44] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.06] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.94] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.45] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.84 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 2.56 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 3.39 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 3.86 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.95] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 5.75 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 2.33 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 8.08 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.58] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.56] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.57] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.61] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.18] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.57] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.56] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 8.76 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 2.08 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 10.84 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 14.41 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<4.38] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<18.79] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 8.90 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B Volatile Organic HAP Emission Test Results2.82 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

11.71 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 4.16 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 194.84 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 199.00 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 10.39 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 109.28 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 119.67 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 7.31 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 48.33 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 55.63 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.16] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<7.41] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<12.57] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.15] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<11.17] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.13] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<8.69] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<13.83] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.42] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.45] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.44] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.01] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.81] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.24 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.46] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.26 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.30 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.10] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.40] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.41 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.10] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.93 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.15] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.88 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.88] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.76] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 1.18 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.04] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<5.16] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<8.68] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<13.83] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.15] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<7.73] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<12.88] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.13] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<8.69] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<13.83] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.98 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 5.20 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 6.18 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.89 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.89 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 1.77 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 2.12 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 1.03 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 3.15 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.88 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.48] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.36] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.20 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.24] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.23 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.08] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.31] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.19] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.14 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.36] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.21] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<0.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<0.76] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.30] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.33] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.07 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.47] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.10] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.57] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.60] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.06] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.66] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.47] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.45] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.92] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.21] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.76] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.40] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.43] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.30] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.33] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.24] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.47] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 38.53 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 11284.48 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B11323.01 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

13.89 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 3952.53 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 3966.42 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 23.61 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 1105.41 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 1129.02 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.84] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.37] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.66] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.45] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.48] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.43] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.46] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<0.42] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.46] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.58] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.56] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.57] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.61] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.18] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.57] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<6.56] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.13 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.59] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.73] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.13 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.81] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.94] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.15 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.45] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.59] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.91] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.21] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<4.12] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.22 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.59] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.81] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.56] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<4.59] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.15] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.70] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.07] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.32] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.39] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.71] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.16] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<8.68] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<13.83] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<5.15] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<7.73] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<12.88] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<5.13] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<8.69] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<13.83] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.40] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.43] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.08 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.07] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.16] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.45] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.11 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.14] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.09 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.32] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.09] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.41] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.44] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.84] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B[<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B

[<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.29] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.99] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.02] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.80] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.82] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.00] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<3.28] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.46 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.86] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.31] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.64 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.82] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.46] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B 0.55 Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.18] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<2.73] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.41] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.44] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.52] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.22] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.03] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.55] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<0.51] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.23] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260B [<1.74] Dry, Standard U.S. EPA Method 0031 with SW -846 Method 8260BData Flag (ADL, BDL, DDL) Test Method Comments lb/mmBtu

DLL [<0.050], 0.630, 0.10 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] ADL 0.15, 0.074, 0.070, [<0.082] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 6.65E-06

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.04E-05] ADL 0.23, 0.15, 0.17, 0.021 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 7.66E-06 DLL 0.27, 1.2, 0.15, 0.048, [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.35E-05]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.11E-05] DLL [<0.050], 0.14, 0.12 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.61E-06] ADL 0.29, 0.18, 0.069, [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.13E-05

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.69E-05] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.98E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.51E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.15E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.59E-06] ADL 0.0087, 0.024, 0.016 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 8.61E-07 ADL 0.0082, [<0.050], 0.0086, [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.63E-06

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 3.49E-06 ADL 0.150, 0.055, 0.079, 0.016 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.02E-06 DLL 0.011, 0.050, 0.012, 0.0088, [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.18E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.20E-06] ADL 0.130, 0.130, 0.076 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 6.08E-06 ADL 0.023, 0.019, 0.011, [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.47E-06

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 8.55E-06 BDL [<0.050], [<0.050], [<0.050] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.65E-06] BDL [<0.050], [<0.050], [<0.050], [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.10E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.75E-06] BDL [<0.050], [<0.050], [<0.050], [<0.050] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.68E-06] BDL [<0.050], [<0.050], [<0.050], [<0.050], [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.76E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.44E-06] BDL [<0.050], [<0.050], [<0.050] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.72E-06] BDL [<0.050], [<0.050], [<0.050], [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.22E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.94E-06] ADL 0.140, 0.190, 0.180 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.01E-06 ADL 0.017, 0.026, 0.037, [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.14E-06

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.12E-05 ADL 0.320, 0.390, 0.180, 0.230 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.50E-05 DLL 0.370, 0.120, 0.110, 0.033, [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.56E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.96E-05] ADL 0.220, 0.140, 0.160 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.41E-06 Volatile Organic HAP Emission Test Results Calculated Emission RateADL 0.041, 0.042, 0.040, [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.98E-06

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.24E-05 BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] ADL 0.110, 0.110, 0.022 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.28E-06 ADL 0.110, 0.140, 0.018, 11.07 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.00E-04

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.05E-04 ADL 0.039, 0.310, 0.440,0.019 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.08E-05 ADL 1.40, 0.370, 0.650, 0.044, 6.03 Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.14E-04

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.25E-04 ADL 0.029, 0.380, 0.018 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 7.73E-06 ADL 0.390, 0.670, 0.017, 1.7472 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 5.11E-05

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 5.89E-05 BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-06] DLL [<0.010], [<0.010], [<0.010], 0.1312 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.62E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.29E-05] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-06] DLL [<0.010], [<0.010], [<0.010], [<0.010] 0.0683 Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.28E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.16E-05] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-06] BDL [<0.010], [<0.010], [<0.010], [<0.2080] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.20E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.46E-05] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], 0.0025, [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.51E-06] DLL 0.0016, 0.0012, [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.32E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.53E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] DLL [<0.025], 0.0034, [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.05E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.93E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] ADL 0.0055, 0.0044, 0.0043 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.51E-07 BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.51E-06] ADL 0.0044, 0.0067, 0.0047, 0.0042 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.68E-07 BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] ADL 0.0087, 0.0039, 0.0050 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 3.19E-07 DLL 0.0028, [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.17E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.48E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] ADL 0.004, 0.017, 0.003 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.35E-07 DLL [<0.010], [<0.010], 0.0028, [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.17E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.60E-06] ADL 0.016, 0.026, 0.012 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.54E-07 BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.21E-06] ADL 0.013, 0.016, 0.030, 0.0096 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.20E-07 DLL [<0.010], 0.004, 0.0043, [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.19E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] ADL 0.027, 0.020, 0.022 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.25E-06 DLL 0.0048, [<0.010], 0.0041, [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.10E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.34E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06]BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-06] BDL [<0.010], [<0.010], [<0.010], [<0.2050] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.93E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.2010] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.06E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-05] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-06] BDL [<0.010], [<0.010], [<0.010], [<0.2080] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.20E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.46E-05] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] ADL 0.033, 0.014, 0.010 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.01E-06 ADL 0.0098, 0.0034, 0.0024, 0.2870 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 5.35E-06

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 6.36E-06 ADL 0.014, 0.019, 0.020, 0.016 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.25E-07 ADL 0.0096, 0.016, 0.019, 0.005, 0.0193 Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.24E-07

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.85E-06 ADL 0.013, 0.010, 0.011 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.25E-06 ADL 0.047, 0.0059, 0.0034, 0.0040 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.09E-06

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 3.34E-06 ADL 0.015, 0.013, 0.023 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.01E-07 DLL 0.0015, [<0.010], [<0.010], 0.0066 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.96E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.40E-06] ADL 0.0036, 0.0046, 0.0035, 0.0042 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.13E-07 BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.29E-06] ADL 0.0043, 0.0037, 0.0054 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.43E-07 DLL 0.0015, [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.14E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.39E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], 0.0011, 0.0017, 0.0018 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.96E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.27E-06] ADL 0.0015, 0.0054, 0.0012 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.47E-07 BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.44E-06] DLL 0.0014, 0.0011, [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.21E-07]DLL [<0.010], [<0.010], [<0.010], 0.0019 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.64E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.84E-07] DLL [<0.010], [<0.010], 0.0019, 0.0013 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.11E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.39E-06] ADL 0.0012, 0.0016, 0.0010 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 6.88E-08 BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.37E-06] DLL 0.0035, 0.0036, [<0.020] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.79E-07] DLL [<0.020], [<0.020], [<0.020], 0.0041 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.13E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] DLL [<0.020], [<0.020], 0.0038, 0.0026 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.22E-07] BDL [<0.020], [<0.020], [<0.020], [<0.020], [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.15E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] DLL 0.0035, 0.0038, [<0.020] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.94E-07] BDL [<0.020], [<0.020], [<0.020], [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.59E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.09E-06] DLL 0.0011, 0.0012, [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.17E-07] DLL [<0.010], [<0.010], [<0.010], 0.0021 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.67E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.85E-07] DLL [<0.010], [<0.010], 0.0011, [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.17E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.49E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], 0.0016, 0.0017, [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.13E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.39E-06] DLL 0.0015, 0.0026, [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.55E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.55E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] ADL 0.360, 0.082, 1.80 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 3.96E-05 ADL 0.420, 0.094, 0.130, 656 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.16E-02ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.16E-02 ADL 0.110, 0.370, 0.500, 0.100 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.45E-05 ADL 0.520, 0.480, 0.560, 0.150, 305.52 Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.12E-03

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.14E-03 ADL 0.770, 0.410, 0.200 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.50E-05 ADL 1.20, 0.530, 0.470, 62.4 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.17E-03

ADL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.19E-03 BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] DLL [<0.025], [<0.025], [<0.025], 0.0152 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.59E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.92E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] DLL [<0.025], [<0.025], [<0.025], [<0.025], 0.0068 Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], [<0.010], [<0.010], 0.0049 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.68E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.54E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], [<0.010], [<0.010], 0.0035 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.49E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.52E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06]DLL [<0.010], [<0.010], [<0.010], 0.0029 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.41E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.52E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.050], [<0.050], [<0.050] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.65E-06] BDL [<0.050], [<0.050], [<0.050], [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.10E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.75E-06] BDL [<0.050], [<0.050], [<0.050], [<0.050] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.68E-06] BDL [<0.050], [<0.050], [<0.050], [<0.050], [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.76E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.44E-06] BDL [<0.050], [<0.050], [<0.050] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.72E-06] BDL [<0.050], [<0.050], [<0.050], [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.22E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.94E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07]BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] ADL 0.0029, 0.0029, 0.0019 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.36E-07 DLL [<0.010], [<0.010], [<0.010], 0.0045 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.10E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.46E-07] ADL 0.0025, 0.0018, 0.0022, 0.0035 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.34E-07 DLL 0.0018, [<0.010], [<0.010], [<0.010], 0.0314 Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.47E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.81E-07] ADL 0.003, 0.003, 0.0025 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.54E-07 DLL 0.0027, [<0.010], [<0.010], 0.0035 Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.74E-07]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.28E-07] DLL [<0.025], [<0.025], 0.0028 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.33E-07] DLL 0.038, 0.036, 0.031, [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.31E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.24E-06] ADL 0.0041, 0.0043, 0.0058, 0.0027 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.27E-07 DLL 0.035, 0.092, 0.045, 0.027, [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.75E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.97E-06] DLL 0.0049, [<0.025], 0.0027 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.90E-07] DLL 0.110, 0.035, 0.040, [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.86E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.45E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.10E-06] DLL [<0.025], [<0.025], [<0.025], 0.0078 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.11E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.42E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.53E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.86E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.22E-06] BDL [<0.10], [<0.10], [<0.10] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-06] BDL [<0.10], [<0.10], [<0.10], [<0.2050] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.93E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] BDL [<0.10], [<0.10], [<0.10], [<0.10] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-06] BDL [<0.10], [<0.10], [<0.10], [<0.10], [<0.2010] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.06E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-05]BDL [<0.10], [<0.10], [<0.10] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-06] BDL [<0.10], [<0.10], [<0.10], [<0.2080] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.20E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.46E-05] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], [<0.010], [<0.010], 0.0011 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.17E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.49E-06] ADL 0.0013, 0.0024, 0.0012 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 8.87E-08 DLL 0.0011, [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.14E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.22E-06] DLL 0.0016, 0.0017, [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.35E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.49E-06] ADL 0.0013, 0.0012, 0.0013, 0.0044 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.10E-07 BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.19E-06] ADL 0.0021, 0.0021, 0.0012 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.78E-08 BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.39E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.34E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.22E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], [<0.010], [<0.010], 0.0017 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.50E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] DLL [<0.025], [<0.025], [<0.025], 0.0053 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.96E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06]BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.33E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.05E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.38E-06] DLL [<0.025], [<0.025], [<0.025], 0.0043 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.06E-06] BDL [<0.025], [<0.025], [<0.025], [<0.025], [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.88E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.94E-06] BDL [<0.025], [<0.025], [<0.025] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.36E-06] BDL [<0.025], [<0.025], [<0.025], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.11E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.47E-06] ADL 0.0096, 0.0090, 0.0081 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.72E-07 DLL 0.0099, 0.0094, 0.0067, [<0.0820] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.91E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] ADL 0.014, 0.015, 0.012, 0.0087 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 6.67E-07 DLL 0.009, 0.021, 0.025, 0.0062, [<0.0804] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.57E-06] ADL 0.014, 0.0083, 0.010 Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 5.85E-07 DLL 0.027, 0.0089, 0.0081, [<0.0832] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.30E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.89E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] DLL [<0.010], [<0.010], [<0.010], 0.0019 Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

DLL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.50E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.30E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0410] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.79E-06] BDL [<0.010], [<0.010], [<0.010], [<0.010] Front half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.36E-07] BDL [<0.010], [<0.010], [<0.010], [<0.010] [<0.0402] Back half fraction consists of 5 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.08E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.61E-06] BDL [<0.010], [<0.010], [<0.010] Incomplete tube analyses for front half fraction. Front half fraction consists of 3 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.43E-07] BDL [<0.010], [<0.010], [<0.010], [<0.0416] Incomplete tube analyses for back half fraction. Back half fraction consists of 4 sample results reported as ug. For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.30E-06]

BDL For M0031 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.84E-06]μg/dscm @ 7% O2

[<14.69] 939 1469 7.4 7.08 939 1469 7.4 [<21.78] 939 1469 7.4 8.10 935 1452 7.2 [<24.79] 935 1452 7.2 [<32.89] 935 1452 7.2 [<5.89] 933 1446 7.3 11.83 933 1446 7.3 [<17.72] 933 1446 7.3 [<0.57] 939 1469 7.4 [<2.11] 939 1469 7.4 [<2.68] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.71] 935 1452 7.2 [<2.27] 935 1452 7.2 [<0.57] 933 1446 7.3 [<2.15] 933 1446 7.3 [<2.72] 933 1446 7.3 0.92 939 1469 7.4 2.80 939 1469 7.4 3.72 939 1469 7.4 4.25 935 1452 7.2 [<2.30] 935 1452 7.2 [<6.55] 935 1452 7.2 6.39 933 1446 7.3 2.59 933 1446 7.3 8.98 933 1446 7.3 [<2.83] 939 1469 7.4 [<4.37] 939 1469 7.4 [<7.20] 939 1469 7.4 [<2.84] 935 1452 7.2 [<3.98] 935 1452 7.2 [<6.81] 935 1452 7.2 [<2.85] 933 1446 7.3 [<4.43] 933 1446 7.3 [<7.29] 933 1446 7.3 9.61 939 1469 7.4 2.28 939 1469 7.4 11.89 939 1469 7.4 15.88 935 1452 7.2 [<4.82] 935 1452 7.2 [<20.71] 935 1452 7.2 9.89 933 1446 7.3 Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%)3.13 933 1446 7.3

13.02 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 4.56 939 1469 7.4 213.59 939 1469 7.4 218.15 939 1469 7.4 11.46 935 1452 7.2 120.45 935 1452 7.2 131.91 935 1452 7.2 8.12 933 1446 7.3 53.70 933 1446 7.3 61.81 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<5.65] 939 1469 7.4 [<8.12] 939 1469 7.4 [<13.77] 939 1469 7.4 [<5.67] 935 1452 7.2 [<6.64] 935 1452 7.2 [<12.31] 935 1452 7.2 [<5.70] 933 1446 7.3 [<9.66] 933 1446 7.3 [<15.36] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.46] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.60] 935 1452 7.2 [<0.24] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.60] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.11] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.10] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3[<3.64] 933 1446 7.3 0.27 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.61] 939 1469 7.4 0.28 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.42] 935 1452 7.2 0.33 933 1446 7.3 [<1.22] 933 1446 7.3 [<1.56] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 0.46 933 1446 7.3 [<1.22] 933 1446 7.3 [<1.68] 933 1446 7.3 1.02 939 1469 7.4 [<1.34] 939 1469 7.4 [<2.35] 939 1469 7.4 0.97 935 1452 7.2 [<0.97] 935 1452 7.2 [<1.94] 935 1452 7.2 1.31 933 1446 7.3 [<1.15] 933 1446 7.3 [<2.46] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3[<5.65] 939 1469 7.4

[<9.51] 939 1469 7.4 [<15.17] 939 1469 7.4 [<5.67] 935 1452 7.2 [<8.52] 935 1452 7.2 [<14.20] 935 1452 7.2 [<5.70] 933 1446 7.3 [<9.66] 933 1446 7.3 [<15.36] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 1.07 939 1469 7.4 5.70 939 1469 7.4 6.77 939 1469 7.4 0.98 935 1452 7.2 0.98 935 1452 7.2 1.96 935 1452 7.2 2.36 933 1446 7.3 1.15 933 1446 7.3 3.50 933 1446 7.3 0.96 939 1469 7.4 [<0.53] 939 1469 7.4 [<1.49] 939 1469 7.4 0.23 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.36] 935 1452 7.2 0.25 933 1446 7.3 [<1.20] 933 1446 7.3 [<1.45] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.21] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.34] 935 1452 7.2 0.15 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.52] 933 1446 7.3 [<0.24] 939 1469 7.4[<0.60] 939 1469 7.4

[<0.84] 939 1469 7.4 [<0.33] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.47] 935 1452 7.2 0.07 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.43] 933 1446 7.3 [<0.51] 939 1469 7.4 [<1.21] 939 1469 7.4 [<1.72] 939 1469 7.4 [<0.66] 935 1452 7.2 [<2.27] 935 1452 7.2 [<2.93] 935 1452 7.2 [<0.52] 933 1446 7.3 [<2.72] 933 1446 7.3 [<3.24] 933 1446 7.3 [<0.23] 939 1469 7.4 [<0.60] 939 1469 7.4 [<0.84] 939 1469 7.4 [<0.44] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.58] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.33] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.47] 935 1452 7.2 [<0.27] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.63] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 42.24 939 1469 7.4 12370.21 939 1469 7.412412.45 939 1469 7.4

15.32 935 1452 7.2 4356.87 935 1452 7.2 4372.19 935 1452 7.2 26.24 933 1446 7.3 1228.23 933 1446 7.3 1254.47 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<1.41] 939 1469 7.4 [<1.70] 939 1469 7.4 [<3.11] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.52] 935 1452 7.2 [<2.93] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.49] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.63] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.48] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.61] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4[<0.47] 935 1452 7.2

[<1.14] 935 1452 7.2 [<1.60] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<2.83] 939 1469 7.4 [<4.37] 939 1469 7.4 [<7.20] 939 1469 7.4 [<2.84] 935 1452 7.2 [<3.98] 935 1452 7.2 [<6.81] 935 1452 7.2 [<2.85] 933 1446 7.3 [<4.43] 933 1446 7.3 [<7.29] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2[<1.14] 935 1452 7.2

[<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 0.15 939 1469 7.4 [<0.65] 939 1469 7.4 [<0.80] 939 1469 7.4 0.14 935 1452 7.2 [<0.90] 935 1452 7.2 [<1.04] 935 1452 7.2 0.16 933 1446 7.3 [<0.50] 933 1446 7.3 [<0.66] 933 1446 7.3 [<0.99] 939 1469 7.4 [<3.52] 939 1469 7.4 [<4.52] 939 1469 7.4 0.24 935 1452 7.2 [<3.96] 935 1452 7.2 [<4.20] 935 1452 7.2 [<0.62] 933 1446 7.3 [<5.10] 933 1446 7.3 [<5.72] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2[<1.70] 935 1452 7.2

[<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.96] 939 1469 7.4 [<4.37] 939 1469 7.4 [<1.17] 935 1452 7.2 [<2.56] 935 1452 7.2 [<3.73] 935 1452 7.2 [<1.43] 933 1446 7.3 [<3.01] 933 1446 7.3 [<4.43] 933 1446 7.3 [<5.65] 939 1469 7.4 [<9.51] 939 1469 7.4 [<15.17] 939 1469 7.4 [<5.67] 935 1452 7.2 [<8.52] 935 1452 7.2 [<14.20] 935 1452 7.2[<5.70] 933 1446 7.3

[<9.66] 933 1446 7.3 [<15.36] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.44] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.58] 935 1452 7.2 0.09 933 1446 7.3 [<1.19] 933 1446 7.3 [<1.29] 933 1446 7.3 [<0.25] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.59] 939 1469 7.4 0.12 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.25] 935 1452 7.2 0.10 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.46] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.42] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.41] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.45] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.59] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.14] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.13] 935 1452 7.2 [<1.43] 933 1446 7.3[<2.22] 933 1446 7.3

[<3.64] 933 1446 7.3 [<1.41] 939 1469 7.4 [<2.19] 939 1469 7.4 [<3.60] 939 1469 7.4 [<1.12] 935 1452 7.2 [<1.99] 935 1452 7.2 [<3.11] 935 1452 7.2 [<1.43] 933 1446 7.3 [<2.22] 933 1446 7.3 [<3.64] 933 1446 7.3 0.50 939 1469 7.4 [<2.03] 939 1469 7.4 [<2.54] 939 1469 7.4 0.70 935 1452 7.2 [<2.01] 935 1452 7.2 [<2.71] 935 1452 7.2 0.61 933 1446 7.3 [<2.42] 933 1446 7.3 [<3.03] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.45] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.59] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.3 [<0.57] 939 1469 7.4 [<1.34] 939 1469 7.4 [<1.90] 939 1469 7.4 [<0.57] 935 1452 7.2 [<1.14] 935 1452 7.2 [<1.70] 935 1452 7.2 [<0.57] 933 1446 7.3 [<1.36] 933 1446 7.3 [<1.93] 933 1446 7.311.20 8.22 368,595 285.3

11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 Flue Gas CO2(%) Flue Gas O2(%) Flue Gas Flow Rate (dscfm) Flue Gas Temperature (F)11.03 8.39 368,102 288.9

11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.911.03 8.39 368,102 288.9

11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.911.20 8.22 368,595 285.3

11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.311.20 8.22 368,595 285.3

11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.311.20 8.22 368,595 285.3

11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.311.13 8.29 367,737 287.1

11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.111.13 8.29 367,737 287.1

11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.111.13 8.29 367,737 287.1

11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.111.03 8.39 368,102 288.9

11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.911.03 8.39 368,102 288.9

11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.20 8.22 368,595 285.3 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.13 8.29 367,737 287.1 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9 11.03 8.39 368,102 288.9Fuel Input Rate Fuel Type Units of Measure Measurement Method

1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other Fuel #11260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day Other 1260 bitum inous ton/day OtherFuel Input Rate Fuel Type Units of Measure Measurement Method

0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other Fuel #20.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute OtherFuel Input Rate Fuel Type Units of Measure Measurement Method Fuel #3Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel #4Other Supporting

InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

Speciated Semi-Volatile Organic HAP Emission Data

2-Methylnaphthalene 1 8/13/2010 2-Methylnaphthalene 1 8/13/2010 2-Methylnaphthalene 1 8/13/2010 2-Methylnaphthalene 1 8/13/2010 2-Methylnaphthalene 2 8/13/2010 2-Methylnaphthalene 2 8/13/2010 2-Methylnaphthalene 2 8/13/2010 2-Methylnaphthalene 2 8/13/2010 2-Methylnaphthalene 3 8/13/2010 2-Methylnaphthalene 3 8/13/2010 2-Methylnaphthalene 3 8/13/2010 2-Methylnaphthalene 3 8/13/2010 Acenaphthene 1 8/13/2010 Acenaphthene 1 8/13/2010 Acenaphthene 1 8/13/2010 Acenaphthene 1 8/13/2010 Acenaphthene 2 8/13/2010 Acenaphthene 2 8/13/2010 Acenaphthene 2 8/13/2010 Acenaphthene 2 8/13/2010 Acenaphthene 3 8/13/2010 Acenaphthene 3 8/13/2010 Acenaphthene 3 8/13/2010 Acenaphthene 3 8/13/2010 Acenaphthylene 1 8/13/2010 Acenaphthylene 1 8/13/2010 Acenaphthylene 1 8/13/2010 Acenaphthylene 1 8/13/2010 Acenaphthylene 2 8/13/2010 Acenaphthylene 2 8/13/2010 Acenaphthylene 2 8/13/2010 Acenaphthylene 2 8/13/2010 Acenaphthylene 3 8/13/2010 Acenaphthylene 3 8/13/2010 Acenaphthylene 3 8/13/2010 Acenaphthylene 3 8/13/2010 Anthracene 1 8/13/2010 Anthracene 1 8/13/2010 Anthracene 1 8/13/2010 Anthracene 1 8/13/2010 Anthracene 2 8/13/2010

Compound (use drop down to define for as many rows as needed) Run Number Test Start DateAnthracene 2 8/13/2010

Anthracene 2 8/13/2010 Anthracene 2 8/13/2010 Anthracene 3 8/13/2010 Anthracene 3 8/13/2010 Anthracene 3 8/13/2010 Anthracene 3 8/13/2010 Benzo(a)anthracene 1 8/13/2010 Benzo(a)anthracene 1 8/13/2010 Benzo(a)anthracene 1 8/13/2010 Benzo(a)anthracene 1 8/13/2010 Benzo(a)anthracene 2 8/13/2010 Benzo(a)anthracene 2 8/13/2010 Benzo(a)anthracene 2 8/13/2010 Benzo(a)anthracene 2 8/13/2010 Benzo(a)anthracene 3 8/13/2010 Benzo(a)anthracene 3 8/13/2010 Benzo(a)anthracene 3 8/13/2010 Benzo(a)anthracene 3 8/13/2010 Benzo(a)pyrene 1 8/13/2010 Benzo(a)pyrene 1 8/13/2010 Benzo(a)pyrene 1 8/13/2010 Benzo(a)pyrene 1 8/13/2010 Benzo(a)pyrene 2 8/13/2010 Benzo(a)pyrene 2 8/13/2010 Benzo(a)pyrene 2 8/13/2010 Benzo(a)pyrene 2 8/13/2010 Benzo(a)pyrene 3 8/13/2010 Benzo(a)pyrene 3 8/13/2010 Benzo(a)pyrene 3 8/13/2010 Benzo(a)pyrene 3 8/13/2010 Benzo(b)fluoranthene 1 8/13/2010 Benzo(b)fluoranthene 1 8/13/2010 Benzo(b)fluoranthene 1 8/13/2010 Benzo(b)fluoranthene 1 8/13/2010 Benzo(b)fluoranthene 2 8/13/2010 Benzo(b)fluoranthene 2 8/13/2010 Benzo(b)fluoranthene 2 8/13/2010 Benzo(b)fluoranthene 2 8/13/2010 Benzo(b)fluoranthene 3 8/13/2010 Benzo(b)fluoranthene 3 8/13/2010 Benzo(b)fluoranthene 3 8/13/2010 Benzo(b)fluoranthene 3 8/13/2010 1-Chloronaphthalene 1 8/13/2010 1-Chloronaphthalene 1 8/13/2010 1-Chloronaphthalene 1 8/13/2010 1-Chloronaphthalene 1 8/13/2010 1-Chloronaphthalene 2 8/13/2010 1-Chloronaphthalene 2 8/13/2010 1-Chloronaphthalene 2 8/13/2010 1-Chloronaphthalene 2 8/13/2010 1-Chloronaphthalene 3 8/13/20101-Chloronaphthalene 3 8/13/2010

1-Chloronaphthalene 3 8/13/2010 1-Chloronaphthalene 3 8/13/2010 Benzo(k)fluoranthene 1 8/13/2010 Benzo(k)fluoranthene 1 8/13/2010 Benzo(k)fluoranthene 1 8/13/2010 Benzo(k)fluoranthene 1 8/13/2010 Benzo(k)fluoranthene 2 8/13/2010 Benzo(k)fluoranthene 2 8/13/2010 Benzo(k)fluoranthene 2 8/13/2010 Benzo(k)fluoranthene 2 8/13/2010 Benzo(k)fluoranthene 3 8/13/2010 Benzo(k)fluoranthene 3 8/13/2010 Benzo(k)fluoranthene 3 8/13/2010 Benzo(k)fluoranthene 3 8/13/2010 Chrysene 1 8/13/2010 Chrysene 1 8/13/2010 Chrysene 1 8/13/2010 Chrysene 1 8/13/2010 Chrysene 2 8/13/2010 Chrysene 2 8/13/2010 Chrysene 2 8/13/2010 Chrysene 2 8/13/2010 Chrysene 3 8/13/2010 Chrysene 3 8/13/2010 Chrysene 3 8/13/2010 Chrysene 3 8/13/2010 Dibenz(a,h)anthracene 1 8/13/2010 Dibenz(a,h)anthracene 1 8/13/2010 Dibenz(a,h)anthracene 1 8/13/2010 Dibenz(a,h)anthracene 1 8/13/2010 Dibenz(a,h)anthracene 2 8/13/2010 Dibenz(a,h)anthracene 2 8/13/2010 Dibenz(a,h)anthracene 2 8/13/2010 Dibenz(a,h)anthracene 2 8/13/2010 Dibenz(a,h)anthracene 3 8/13/2010 Dibenz(a,h)anthracene 3 8/13/2010 Dibenz(a,h)anthracene 3 8/13/2010 Dibenz(a,h)anthracene 3 8/13/2010 Fluoranthene 1 8/13/2010 Fluoranthene 1 8/13/2010 Fluoranthene 1 8/13/2010 Fluoranthene 1 8/13/2010 Fluoranthene 2 8/13/2010 Fluoranthene 2 8/13/2010 Fluoranthene 2 8/13/2010 Fluoranthene 2 8/13/2010 Fluoranthene 3 8/13/2010 Fluoranthene 3 8/13/2010 Fluoranthene 3 8/13/2010 Fluoranthene 3 8/13/2010 Fluorene 1 8/13/2010Fluorene 1 8/13/2010

Fluorene 1 8/13/2010 Fluorene 1 8/13/2010 Fluorene 2 8/13/2010 Fluorene 2 8/13/2010 Fluorene 2 8/13/2010 Fluorene 2 8/13/2010 Fluorene 3 8/13/2010 Fluorene 3 8/13/2010 Fluorene 3 8/13/2010 Fluorene 3 8/13/2010 Indeno(1,2,3-cd)pyrene 1 8/13/2010 Indeno(1,2,3-cd)pyrene 1 8/13/2010 Indeno(1,2,3-cd)pyrene 1 8/13/2010 Indeno(1,2,3-cd)pyrene 1 8/13/2010 Indeno(1,2,3-cd)pyrene 2 8/13/2010 Indeno(1,2,3-cd)pyrene 2 8/13/2010 Indeno(1,2,3-cd)pyrene 2 8/13/2010 Indeno(1,2,3-cd)pyrene 2 8/13/2010 Indeno(1,2,3-cd)pyrene 3 8/13/2010 Indeno(1,2,3-cd)pyrene 3 8/13/2010 Indeno(1,2,3-cd)pyrene 3 8/13/2010 Indeno(1,2,3-cd)pyrene 3 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 1 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 2 8/13/2010 Naphthalene 3 8/13/2010 Naphthalene 3 8/13/2010 Naphthalene 3 8/13/2010 Naphthalene 3 8/13/2010 Phenanthrene 1 8/13/2010 Phenanthrene 1 8/13/2010 Phenanthrene 1 8/13/2010 Phenanthrene 1 8/13/2010 Phenanthrene 2 8/13/2010 Phenanthrene 2 8/13/2010 Phenanthrene 2 8/13/2010 Phenanthrene 2 8/13/2010 Phenanthrene 3 8/13/2010 Phenanthrene 3 8/13/2010 Phenanthrene 3 8/13/2010 Phenanthrene 3 8/13/2010 Pyrene 1 8/13/2010 Pyrene 1 8/13/2010 Pyrene 1 8/13/2010 Pyrene 1 8/13/2010 Pyrene 2 8/13/2010Pyrene 2 8/13/2010

Pyrene 2 8/13/2010 Pyrene 2 8/13/2010 Pyrene 3 8/13/2010 Pyrene 3 8/13/2010 Pyrene 3 8/13/2010 Pyrene 3 8/13/2010 1-Methylnaphthalene 1 8/13/2010 1-Methylnaphthalene 1 8/13/2010 1-Methylnaphthalene 1 8/13/2010 1-Methylnaphthalene 1 8/13/2010 1-Methylnaphthalene 2 8/13/2010 1-Methylnaphthalene 2 8/13/2010 1-Methylnaphthalene 2 8/13/2010 1-Methylnaphthalene 2 8/13/2010 1-Methylnaphthalene 3 8/13/2010 1-Methylnaphthalene 3 8/13/2010 1-Methylnaphthalene 3 8/13/2010 1-Methylnaphthalene 3 8/13/2010 1-Methylphenanthrene 1 8/13/2010 1-Methylphenanthrene 1 8/13/2010 1-Methylphenanthrene 1 8/13/2010 1-Methylphenanthrene 1 8/13/2010 1-Methylphenanthrene 2 8/13/2010 1-Methylphenanthrene 2 8/13/2010 1-Methylphenanthrene 2 8/13/2010 1-Methylphenanthrene 2 8/13/2010 1-Methylphenanthrene 3 8/13/2010 1-Methylphenanthrene 3 8/13/2010 1-Methylphenanthrene 3 8/13/2010 1-Methylphenanthrene 3 8/13/2010 2,4-Dimethylphenol 1 8/13/2010 2,4-Dimethylphenol 1 8/13/2010 2,4-Dimethylphenol 1 8/13/2010 2,4-Dimethylphenol 1 8/13/2010 2,4-Dimethylphenol 2 8/13/2010 2,4-Dimethylphenol 2 8/13/2010 2,4-Dimethylphenol 2 8/13/2010 2,4-Dimethylphenol 2 8/13/2010 2,4-Dimethylphenol 3 8/13/2010 2,4-Dimethylphenol 3 8/13/2010 2,4-Dimethylphenol 3 8/13/2010 2,4-Dimethylphenol 3 8/13/2010 Aniline 1 8/13/2010 Aniline 1 8/13/2010 Aniline 1 8/13/2010 Aniline 1 8/13/2010 Aniline 2 8/13/2010 Aniline 2 8/13/2010 Aniline 2 8/13/2010 Aniline 2 8/13/2010 Aniline 3 8/13/2010Aniline 3 8/13/2010

Aniline 3 8/13/2010 Aniline 3 8/13/2010 Benzyl alcohol 1 8/13/2010 Benzyl alcohol 1 8/13/2010 Benzyl alcohol 1 8/13/2010 Benzyl alcohol 1 8/13/2010 Benzyl alcohol 2 8/13/2010 Benzyl alcohol 2 8/13/2010 Benzyl alcohol 2 8/13/2010 Benzyl alcohol 2 8/13/2010 Benzyl alcohol 3 8/13/2010 Benzyl alcohol 3 8/13/2010 Benzyl alcohol 3 8/13/2010 Benzyl alcohol 3 8/13/2010 Bis(2-chloroethoxy)methane 1 8/13/2010 Bis(2-chloroethoxy)methane 1 8/13/2010 Bis(2-chloroethoxy)methane 1 8/13/2010 Bis(2-chloroethoxy)methane 1 8/13/2010 Bis(2-chloroethoxy)methane 2 8/13/2010 Bis(2-chloroethoxy)methane 2 8/13/2010 Bis(2-chloroethoxy)methane 2 8/13/2010 Bis(2-chloroethoxy)methane 2 8/13/2010 Bis(2-chloroethoxy)methane 3 8/13/2010 Bis(2-chloroethoxy)methane 3 8/13/2010 Bis(2-chloroethoxy)methane 3 8/13/2010 Bis(2-chloroethoxy)methane 3 8/13/2010 Bis(2-chloroethyl) ether 1 8/13/2010 Bis(2-chloroethyl) ether 1 8/13/2010 Bis(2-chloroethyl) ether 1 8/13/2010 Bis(2-chloroethyl) ether 1 8/13/2010 Bis(2-chloroethyl) ether 2 8/13/2010 Bis(2-chloroethyl) ether 2 8/13/2010 Bis(2-chloroethyl) ether 2 8/13/2010 Bis(2-chloroethyl) ether 2 8/13/2010 Bis(2-chloroethyl) ether 3 8/13/2010 Bis(2-chloroethyl) ether 3 8/13/2010 Bis(2-chloroethyl) ether 3 8/13/2010 Bis(2-chloroethyl) ether 3 8/13/2010 Bis(2-chloroisopropyl) ether 1 8/13/2010 Bis(2-chloroisopropyl) ether 1 8/13/2010 Bis(2-chloroisopropyl) ether 1 8/13/2010 Bis(2-chloroisopropyl) ether 1 8/13/2010 Bis(2-chloroisopropyl) ether 2 8/13/2010 Bis(2-chloroisopropyl) ether 2 8/13/2010 Bis(2-chloroisopropyl) ether 2 8/13/2010 Bis(2-chloroisopropyl) ether 2 8/13/2010 Bis(2-chloroisopropyl) ether 3 8/13/2010 Bis(2-chloroisopropyl) ether 3 8/13/2010 Bis(2-chloroisopropyl) ether 3 8/13/2010 Bis(2-chloroisopropyl) ether 3 8/13/2010 Bis(2-ethylhexyl) phthalate 1 8/13/2010Bis(2-ethylhexyl) phthalate 1 8/13/2010

Bis(2-ethylhexyl) phthalate 1 8/13/2010 Bis(2-ethylhexyl) phthalate 1 8/13/2010 Bis(2-ethylhexyl) phthalate 2 8/13/2010 Bis(2-ethylhexyl) phthalate 2 8/13/2010 Bis(2-ethylhexyl) phthalate 2 8/13/2010 Bis(2-ethylhexyl) phthalate 2 8/13/2010 Bis(2-ethylhexyl) phthalate 3 8/13/2010 Bis(2-ethylhexyl) phthalate 3 8/13/2010 Bis(2-ethylhexyl) phthalate 3 8/13/2010 Bis(2-ethylhexyl) phthalate 3 8/13/2010 4-Bromophenyl phenyl ether 1 8/13/2010 4-Bromophenyl phenyl ether 1 8/13/2010 4-Bromophenyl phenyl ether 1 8/13/2010 4-Bromophenyl phenyl ether 1 8/13/2010 4-Bromophenyl phenyl ether 2 8/13/2010 4-Bromophenyl phenyl ether 2 8/13/2010 4-Bromophenyl phenyl ether 2 8/13/2010 4-Bromophenyl phenyl ether 2 8/13/2010 4-Bromophenyl phenyl ether 3 8/13/2010 4-Bromophenyl phenyl ether 3 8/13/2010 4-Bromophenyl phenyl ether 3 8/13/2010 4-Bromophenyl phenyl ether 3 8/13/2010 Butyl benzyl phthalate 1 8/13/2010 Butyl benzyl phthalate 1 8/13/2010 Butyl benzyl phthalate 1 8/13/2010 Butyl benzyl phthalate 1 8/13/2010 Butyl benzyl phthalate 2 8/13/2010 Butyl benzyl phthalate 2 8/13/2010 Butyl benzyl phthalate 2 8/13/2010 Butyl benzyl phthalate 2 8/13/2010 Butyl benzyl phthalate 3 8/13/2010 Butyl benzyl phthalate 3 8/13/2010 Butyl benzyl phthalate 3 8/13/2010 Butyl benzyl phthalate 3 8/13/2010 4-Chloroaniline 1 8/13/2010 4-Chloroaniline 1 8/13/2010 4-Chloroaniline 1 8/13/2010 4-Chloroaniline 1 8/13/2010 4-Chloroaniline 2 8/13/2010 4-Chloroaniline 2 8/13/2010 4-Chloroaniline 2 8/13/2010 4-Chloroaniline 2 8/13/2010 4-Chloroaniline 3 8/13/2010 4-Chloroaniline 3 8/13/2010 4-Chloroaniline 3 8/13/2010 4-Chloroaniline 3 8/13/2010 4-Chloro-3-methylphenol 1 8/13/2010 4-Chloro-3-methylphenol 1 8/13/2010 4-Chloro-3-methylphenol 1 8/13/2010 4-Chloro-3-methylphenol 1 8/13/2010 4-Chloro-3-methylphenol 2 8/13/20104-Chloro-3-methylphenol 2 8/13/2010

4-Chloro-3-methylphenol 2 8/13/2010 4-Chloro-3-methylphenol 2 8/13/2010 4-Chloro-3-methylphenol 3 8/13/2010 4-Chloro-3-methylphenol 3 8/13/2010 4-Chloro-3-methylphenol 3 8/13/2010 4-Chloro-3-methylphenol 3 8/13/2010 2-Chloronaphthalene 1 8/13/2010 2-Chloronaphthalene 1 8/13/2010 2-Chloronaphthalene 1 8/13/2010 2-Chloronaphthalene 1 8/13/2010 2-Chloronaphthalene 2 8/13/2010 2-Chloronaphthalene 2 8/13/2010 2-Chloronaphthalene 2 8/13/2010 2-Chloronaphthalene 2 8/13/2010 2-Chloronaphthalene 3 8/13/2010 2-Chloronaphthalene 3 8/13/2010 2-Chloronaphthalene 3 8/13/2010 2-Chloronaphthalene 3 8/13/2010 2-Chlorophenol 1 8/13/2010 2-Chlorophenol 1 8/13/2010 2-Chlorophenol 1 8/13/2010 2-Chlorophenol 1 8/13/2010 2-Chlorophenol 2 8/13/2010 2-Chlorophenol 2 8/13/2010 2-Chlorophenol 2 8/13/2010 2-Chlorophenol 2 8/13/2010 2-Chlorophenol 3 8/13/2010 2-Chlorophenol 3 8/13/2010 2-Chlorophenol 3 8/13/2010 2-Chlorophenol 3 8/13/2010 4-Chlorophenyl phenyl ether 1 8/13/2010 4-Chlorophenyl phenyl ether 1 8/13/2010 4-Chlorophenyl phenyl ether 1 8/13/2010 4-Chlorophenyl phenyl ether 1 8/13/2010 4-Chlorophenyl phenyl ether 2 8/13/2010 4-Chlorophenyl phenyl ether 2 8/13/2010 4-Chlorophenyl phenyl ether 2 8/13/2010 4-Chlorophenyl phenyl ether 2 8/13/2010 4-Chlorophenyl phenyl ether 3 8/13/2010 4-Chlorophenyl phenyl ether 3 8/13/2010 4-Chlorophenyl phenyl ether 3 8/13/2010 4-Chlorophenyl phenyl ether 3 8/13/2010 Dibenzofuran 1 8/13/2010 Dibenzofuran 1 8/13/2010 Dibenzofuran 1 8/13/2010 Dibenzofuran 1 8/13/2010 Dibenzofuran 2 8/13/2010 Dibenzofuran 2 8/13/2010 Dibenzofuran 2 8/13/2010 Dibenzofuran 2 8/13/2010 Dibenzofuran 3 8/13/2010Dibenzofuran 3 8/13/2010

Dibenzofuran 3 8/13/2010 Dibenzofuran 3 8/13/2010 Di-n-butyl phthalate 1 8/13/2010 Di-n-butyl phthalate 1 8/13/2010 Di-n-butyl phthalate 1 8/13/2010 Di-n-butyl phthalate 1 8/13/2010 Di-n-butyl phthalate 2 8/13/2010 Di-n-butyl phthalate 2 8/13/2010 Di-n-butyl phthalate 2 8/13/2010 Di-n-butyl phthalate 2 8/13/2010 Di-n-butyl phthalate 3 8/13/2010 Di-n-butyl phthalate 3 8/13/2010 Di-n-butyl phthalate 3 8/13/2010 Di-n-butyl phthalate 3 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 1 8/13/2010 1,2-Dichlorobenzene 2 8/13/2010 1,2-Dichlorobenzene 2 8/13/2010 1,2-Dichlorobenzene 2 8/13/2010 1,2-Dichlorobenzene 2 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,2-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 1 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 2 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,3-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 1 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 2 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 1,4-Dichlorobenzene 3 8/13/2010 2,4-Dichlorophenol 1 8/13/20102,4-Dichlorophenol 1 8/13/2010

2,4-Dichlorophenol 1 8/13/2010 2,4-Dichlorophenol 1 8/13/2010 2,4-Dichlorophenol 2 8/13/2010 2,4-Dichlorophenol 2 8/13/2010 2,4-Dichlorophenol 2 8/13/2010 2,4-Dichlorophenol 2 8/13/2010 2,4-Dichlorophenol 3 8/13/2010 2,4-Dichlorophenol 3 8/13/2010 2,4-Dichlorophenol 3 8/13/2010 2,4-Dichlorophenol 3 8/13/2010 Trifluralin 1 8/13/2010 2-Methylanthracene 1 8/13/2010 2-Methylanthracene 1 8/13/2010 2-Methylanthracene 1 8/13/2010 2-Methylanthracene 2 8/13/2010 2-Methylanthracene 2 8/13/2010 2-Methylanthracene 2 8/13/2010 2-Methylanthracene 2 8/13/2010 2-Methylanthracene 3 8/13/2010 2-Methylanthracene 3 8/13/2010 2-Methylanthracene 3 8/13/2010 2-Methylanthracene 3 8/13/2010 Diethyl phthalate 1 8/13/2010 Diethyl phthalate 1 8/13/2010 Diethyl phthalate 1 8/13/2010 Diethyl phthalate 1 8/13/2010 Diethyl phthalate 2 8/13/2010 Diethyl phthalate 2 8/13/2010 Diethyl phthalate 2 8/13/2010 Diethyl phthalate 2 8/13/2010 Diethyl phthalate 3 8/13/2010 Diethyl phthalate 3 8/13/2010 Diethyl phthalate 3 8/13/2010 Diethyl phthalate 3 8/13/2010 Dim ethyl phthalate 1 8/13/2010 Dim ethyl phthalate 1 8/13/2010 Dim ethyl phthalate 1 8/13/2010 Dim ethyl phthalate 1 8/13/2010 Dim ethyl phthalate 2 8/13/2010 Dim ethyl phthalate 2 8/13/2010 Dim ethyl phthalate 2 8/13/2010 Dim ethyl phthalate 2 8/13/2010 Dim ethyl phthalate 3 8/13/2010 Dim ethyl phthalate 3 8/13/2010 Dim ethyl phthalate 3 8/13/2010 Dim ethyl phthalate 3 8/13/2010 2,4-Dinitrophenol 1 8/13/2010 2,4-Dinitrophenol 1 8/13/2010 2,4-Dinitrophenol 1 8/13/2010 2,4-Dinitrophenol 1 8/13/2010 2,4-Dinitrophenol 2 8/13/20102,4-Dinitrophenol 2 8/13/2010

2,4-Dinitrophenol 2 8/13/2010 2,4-Dinitrophenol 2 8/13/2010 2,4-Dinitrophenol 3 8/13/2010 2,4-Dinitrophenol 3 8/13/2010 2,4-Dinitrophenol 3 8/13/2010 2,4-Dinitrophenol 3 8/13/2010 2,4-Dinitrotoluene 1 8/13/2010 2,4-Dinitrotoluene 1 8/13/2010 2,4-Dinitrotoluene 1 8/13/2010 2,4-Dinitrotoluene 1 8/13/2010 2,4-Dinitrotoluene 2 8/13/2010 2,4-Dinitrotoluene 2 8/13/2010 2,4-Dinitrotoluene 2 8/13/2010 2,4-Dinitrotoluene 2 8/13/2010 2,4-Dinitrotoluene 3 8/13/2010 2,4-Dinitrotoluene 3 8/13/2010 2,4-Dinitrotoluene 3 8/13/2010 2,4-Dinitrotoluene 3 8/13/2010 2,6-Dinitrotoluene 1 8/13/2010 2,6-Dinitrotoluene 1 8/13/2010 2,6-Dinitrotoluene 1 8/13/2010 2,6-Dinitrotoluene 1 8/13/2010 2,6-Dinitrotoluene 2 8/13/2010 2,6-Dinitrotoluene 2 8/13/2010 2,6-Dinitrotoluene 2 8/13/2010 2,6-Dinitrotoluene 2 8/13/2010 2,6-Dinitrotoluene 3 8/13/2010 2,6-Dinitrotoluene 3 8/13/2010 2,6-Dinitrotoluene 3 8/13/2010 2,6-Dinitrotoluene 3 8/13/2010 3,3'-Dichlorobenzidine 1 8/13/2010 3,3'-Dichlorobenzidine 1 8/13/2010 3,3'-Dichlorobenzidine 1 8/13/2010 3,3'-Dichlorobenzidine 1 8/13/2010 3,3'-Dichlorobenzidine 2 8/13/2010 3,3'-Dichlorobenzidine 2 8/13/2010 3,3'-Dichlorobenzidine 2 8/13/2010 3,3'-Dichlorobenzidine 2 8/13/2010 3,3'-Dichlorobenzidine 3 8/13/2010 3,3'-Dichlorobenzidine 3 8/13/2010 3,3'-Dichlorobenzidine 3 8/13/2010 3,3'-Dichlorobenzidine 3 8/13/2010 3-Methylcholanthrene 1 8/13/2010 3-Methylcholanthrene 1 8/13/2010 3-Methylcholanthrene 1 8/13/2010 3-Methylcholanthrene 1 8/13/2010 3-Methylcholanthrene 2 8/13/2010 3-Methylcholanthrene 2 8/13/2010 3-Methylcholanthrene 2 8/13/2010 3-Methylcholanthrene 2 8/13/2010 3-Methylcholanthrene 3 8/13/20103-Methylcholanthrene 3 8/13/2010

3-Methylcholanthrene 3 8/13/2010 3-Methylcholanthrene 3 8/13/2010 Di-n-octyl phthalate 1 8/13/2010 Di-n-octyl phthalate 1 8/13/2010 Di-n-octyl phthalate 1 8/13/2010 Di-n-octyl phthalate 1 8/13/2010 Di-n-octyl phthalate 2 8/13/2010 Di-n-octyl phthalate 2 8/13/2010 Di-n-octyl phthalate 2 8/13/2010 Di-n-octyl phthalate 2 8/13/2010 Di-n-octyl phthalate 3 8/13/2010 Di-n-octyl phthalate 3 8/13/2010 Di-n-octyl phthalate 3 8/13/2010 Di-n-octyl phthalate 3 8/13/2010 4,6-Dinitro-2-methylphenol 1 8/13/2010 4,6-Dinitro-2-methylphenol 1 8/13/2010 4,6-Dinitro-2-methylphenol 1 8/13/2010 4,6-Dinitro-2-methylphenol 1 8/13/2010 4,6-Dinitro-2-methylphenol 2 8/13/2010 4,6-Dinitro-2-methylphenol 2 8/13/2010 4,6-Dinitro-2-methylphenol 2 8/13/2010 4,6-Dinitro-2-methylphenol 2 8/13/2010 4,6-Dinitro-2-methylphenol 3 8/13/2010 4,6-Dinitro-2-methylphenol 3 8/13/2010 4,6-Dinitro-2-methylphenol 3 8/13/2010 4,6-Dinitro-2-methylphenol 3 8/13/2010 Hexachlorobenzene 1 8/13/2010 Hexachlorobenzene 1 8/13/2010 Hexachlorobenzene 1 8/13/2010 Hexachlorobenzene 1 8/13/2010 Hexachlorobenzene 2 8/13/2010 Hexachlorobenzene 2 8/13/2010 Hexachlorobenzene 2 8/13/2010 Hexachlorobenzene 2 8/13/2010 Hexachlorobenzene 3 8/13/2010 Hexachlorobenzene 3 8/13/2010 Hexachlorobenzene 3 8/13/2010 Hexachlorobenzene 3 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 1 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 2 8/13/2010 Hexachlorobutadiene 3 8/13/2010 Hexachlorobutadiene 3 8/13/2010 Hexachlorobutadiene 3 8/13/2010 Hexachlorobutadiene 3 8/13/2010 Hexachlorocyclopentadiene 1 8/13/2010Hexachlorocyclopentadiene 1 8/13/2010

Hexachlorocyclopentadiene 1 8/13/2010 Hexachlorocyclopentadiene 1 8/13/2010 Hexachlorocyclopentadiene 2 8/13/2010 Hexachlorocyclopentadiene 2 8/13/2010 Hexachlorocyclopentadiene 2 8/13/2010 Hexachlorocyclopentadiene 2 8/13/2010 Hexachlorocyclopentadiene 3 8/13/2010 Hexachlorocyclopentadiene 3 8/13/2010 Hexachlorocyclopentadiene 3 8/13/2010 Hexachlorocyclopentadiene 3 8/13/2010 Hexachloroethane 1 8/13/2010 Hexachloroethane 1 8/13/2010 Hexachloroethane 1 8/13/2010 Hexachloroethane 1 8/13/2010 Hexachloroethane 2 8/13/2010 Hexachloroethane 2 8/13/2010 Hexachloroethane 2 8/13/2010 Hexachloroethane 2 8/13/2010 Hexachloroethane 3 8/13/2010 Hexachloroethane 3 8/13/2010 Hexachloroethane 3 8/13/2010 Hexachloroethane 3 8/13/2010 7,12-Dimethylbenz(a)-anthracene 1 8/13/2010 7,12-Dimethylbenz(a)-anthracene 1 8/13/2010 7,12-Dimethylbenz(a)-anthracene 1 8/13/2010 7,12-Dimethylbenz(a)-anthracene 1 8/13/2010 7,12-Dimethylbenz(a)-anthracene 2 8/13/2010 7,12-Dimethylbenz(a)-anthracene 2 8/13/2010 7,12-Dimethylbenz(a)-anthracene 2 8/13/2010 7,12-Dimethylbenz(a)-anthracene 2 8/13/2010 7,12-Dimethylbenz(a)-anthracene 3 8/13/2010 7,12-Dimethylbenz(a)-anthracene 3 8/13/2010 7,12-Dimethylbenz(a)-anthracene 3 8/13/2010 7,12-Dimethylbenz(a)-anthracene 3 8/13/2010 Isophorone 1 8/13/2010 Isophorone 1 8/13/2010 Isophorone 1 8/13/2010 Isophorone 1 8/13/2010 Isophorone 2 8/13/2010 Isophorone 2 8/13/2010 Isophorone 2 8/13/2010 Isophorone 2 8/13/2010 Isophorone 3 8/13/2010 Isophorone 3 8/13/2010 Isophorone 3 8/13/2010 Isophorone 3 8/13/2010 9,10-Dimethylanthracene 1 8/13/2010 9,10-Dimethylanthracene 1 8/13/2010 9,10-Dimethylanthracene 1 8/13/2010 9,10-Dimethylanthracene 1 8/13/2010 9,10-Dimethylanthracene 2 8/13/20109,10-Dimethylanthracene 2 8/13/2010

9,10-Dimethylanthracene 2 8/13/2010 9,10-Dimethylanthracene 2 8/13/2010 9,10-Dimethylanthracene 3 8/13/2010 9,10-Dimethylanthracene 3 8/13/2010 9,10-Dimethylanthracene 3 8/13/2010 9,10-Dimethylanthracene 3 8/13/2010 Benzidine 1 8/13/2010 Benzidine 1 8/13/2010 Benzidine 1 8/13/2010 Benzidine 1 8/13/2010 Benzidine 2 8/13/2010 Benzidine 2 8/13/2010 Benzidine 2 8/13/2010 Benzidine 2 8/13/2010 Benzidine 3 8/13/2010 Benzidine 3 8/13/2010 Benzidine 3 8/13/2010 Benzidine 3 8/13/2010 2-Methylphenol 1 8/13/2010 2-Methylphenol 1 8/13/2010 2-Methylphenol 1 8/13/2010 2-Methylphenol 1 8/13/2010 2-Methylphenol 2 8/13/2010 2-Methylphenol 2 8/13/2010 2-Methylphenol 2 8/13/2010 2-Methylphenol 2 8/13/2010 2-Methylphenol 3 8/13/2010 2-Methylphenol 3 8/13/2010 2-Methylphenol 3 8/13/2010 2-Methylphenol 3 8/13/2010 3&4-Methylphenol 1 8/13/2010 3&4-Methylphenol 1 8/13/2010 3&4-Methylphenol 1 8/13/2010 3&4-Methylphenol 1 8/13/2010 3&4-Methylphenol 2 8/13/2010 3&4-Methylphenol 2 8/13/2010 3&4-Methylphenol 2 8/13/2010 3&4-Methylphenol 2 8/13/2010 3&4-Methylphenol 3 8/13/2010 3&4-Methylphenol 3 8/13/2010 3&4-Methylphenol 3 8/13/2010 3&4-Methylphenol 3 8/13/2010 Benzo(a)fluorene 1 8/13/2010 Benzo(a)fluorene 1 8/13/2010 Benzo(a)fluorene 1 8/13/2010 Benzo(a)fluorene 1 8/13/2010 Benzo(a)fluorene 2 8/13/2010 Benzo(a)fluorene 2 8/13/2010 Benzo(a)fluorene 2 8/13/2010 Benzo(a)fluorene 2 8/13/2010 Benzo(a)fluorene 3 8/13/2010Benzo(a)fluorene 3 8/13/2010

Benzo(a)fluorene 3 8/13/2010 Benzo(a)fluorene 3 8/13/2010 Di-n-butyl phthalate 1 8/13/2010 Benzo(b)fluorene 1 8/13/2010 Benzo(b)fluorene 1 8/13/2010 Benzo(b)fluorene 1 8/13/2010 Benzo(b)fluorene 2 8/13/2010 Benzo(b)fluorene 2 8/13/2010 Benzo(b)fluorene 2 8/13/2010 Benzo(b)fluorene 2 8/13/2010 Benzo(b)fluorene 3 8/13/2010 Benzo(b)fluorene 3 8/13/2010 Benzo(b)fluorene 3 8/13/2010 Benzo(b)fluorene 3 8/13/2010 2-Nitroaniline 1 8/13/2010 2-Nitroaniline 1 8/13/2010 2-Nitroaniline 1 8/13/2010 2-Nitroaniline 1 8/13/2010 2-Nitroaniline 2 8/13/2010 2-Nitroaniline 2 8/13/2010 2-Nitroaniline 2 8/13/2010 2-Nitroaniline 2 8/13/2010 2-Nitroaniline 3 8/13/2010 2-Nitroaniline 3 8/13/2010 2-Nitroaniline 3 8/13/2010 2-Nitroaniline 3 8/13/2010 3-Nitroaniline 1 8/13/2010 3-Nitroaniline 1 8/13/2010 3-Nitroaniline 1 8/13/2010 3-Nitroaniline 1 8/13/2010 3-Nitroaniline 2 8/13/2010 3-Nitroaniline 2 8/13/2010 3-Nitroaniline 2 8/13/2010 3-Nitroaniline 2 8/13/2010 3-Nitroaniline 3 8/13/2010 3-Nitroaniline 3 8/13/2010 3-Nitroaniline 3 8/13/2010 3-Nitroaniline 3 8/13/2010 4-Nitroaniline 1 8/13/2010 4-Nitroaniline 1 8/13/2010 4-Nitroaniline 1 8/13/2010 4-Nitroaniline 1 8/13/2010 4-Nitroaniline 2 8/13/2010 4-Nitroaniline 2 8/13/2010 4-Nitroaniline 2 8/13/2010 4-Nitroaniline 2 8/13/2010 4-Nitroaniline 3 8/13/2010 4-Nitroaniline 3 8/13/2010 4-Nitroaniline 3 8/13/2010 4-Nitroaniline 3 8/13/2010 Nitrobenzene 1 8/13/2010Nitrobenzene 1 8/13/2010

Nitrobenzene 1 8/13/2010 Nitrobenzene 1 8/13/2010 Nitrobenzene 2 8/13/2010 Nitrobenzene 2 8/13/2010 Nitrobenzene 2 8/13/2010 Nitrobenzene 2 8/13/2010 Nitrobenzene 3 8/13/2010 Nitrobenzene 3 8/13/2010 Nitrobenzene 3 8/13/2010 Nitrobenzene 3 8/13/2010 2-Nitrophenol 1 8/13/2010 2-Nitrophenol 1 8/13/2010 2-Nitrophenol 1 8/13/2010 2-Nitrophenol 1 8/13/2010 2-Nitrophenol 2 8/13/2010 2-Nitrophenol 2 8/13/2010 2-Nitrophenol 2 8/13/2010 2-Nitrophenol 2 8/13/2010 2-Nitrophenol 3 8/13/2010 2-Nitrophenol 3 8/13/2010 2-Nitrophenol 3 8/13/2010 2-Nitrophenol 3 8/13/2010 4-Nitrophenol 1 8/13/2010 4-Nitrophenol 1 8/13/2010 4-Nitrophenol 1 8/13/2010 4-Nitrophenol 1 8/13/2010 4-Nitrophenol 2 8/13/2010 4-Nitrophenol 2 8/13/2010 4-Nitrophenol 2 8/13/2010 4-Nitrophenol 2 8/13/2010 4-Nitrophenol 3 8/13/2010 4-Nitrophenol 3 8/13/2010 4-Nitrophenol 3 8/13/2010 4-Nitrophenol 3 8/13/2010 2,4-Dichlorophenol 1 8/13/2010 Benzo(e)pyrene 1 8/13/2010 Benzo(e)pyrene 1 8/13/2010 Benzo(e)pyrene 1 8/13/2010 Benzo(e)pyrene 2 8/13/2010 Benzo(e)pyrene 2 8/13/2010 Benzo(e)pyrene 2 8/13/2010 Benzo(e)pyrene 2 8/13/2010 Benzo(e)pyrene 3 8/13/2010 Benzo(e)pyrene 3 8/13/2010 Benzo(e)pyrene 3 8/13/2010 Benzo(e)pyrene 3 8/13/2010 Benzoic acid 1 8/13/2010 Benzoic acid 1 8/13/2010 Benzoic acid 1 8/13/2010 Benzoic acid 1 8/13/2010 Benzoic acid 2 8/13/2010Benzoic acid 2 8/13/2010

Benzoic acid 2 8/13/2010 Benzoic acid 2 8/13/2010 Benzoic acid 3 8/13/2010 Benzoic acid 3 8/13/2010 Benzoic acid 3 8/13/2010 Benzoic acid 3 8/13/2010 Biphenyl 1 8/13/2010 Biphenyl 1 8/13/2010 Biphenyl 1 8/13/2010 Biphenyl 1 8/13/2010 Biphenyl 2 8/13/2010 Biphenyl 2 8/13/2010 Biphenyl 2 8/13/2010 Biphenyl 2 8/13/2010 Biphenyl 3 8/13/2010 Biphenyl 3 8/13/2010 Biphenyl 3 8/13/2010 Biphenyl 3 8/13/2010 N-Nitrosodi-n-propylam ine 1 8/13/2010 N-Nitrosodi-n-propylam ine 1 8/13/2010 N-Nitrosodi-n-propylam ine 1 8/13/2010 N-Nitrosodi-n-propylam ine 1 8/13/2010 N-Nitrosodi-n-propylam ine 2 8/13/2010 N-Nitrosodi-n-propylam ine 2 8/13/2010 N-Nitrosodi-n-propylam ine 2 8/13/2010 N-Nitrosodi-n-propylam ine 2 8/13/2010 N-Nitrosodi-n-propylam ine 3 8/13/2010 N-Nitrosodi-n-propylam ine 3 8/13/2010 N-Nitrosodi-n-propylam ine 3 8/13/2010 N-Nitrosodi-n-propylam ine 3 8/13/2010 Carbozole 1 8/13/2010 Carbozole 1 8/13/2010 Carbozole 1 8/13/2010 Carbozole 1 8/13/2010 Carbozole 2 8/13/2010 Carbozole 2 8/13/2010 Carbozole 2 8/13/2010 Carbozole 2 8/13/2010 Carbozole 3 8/13/2010 Carbozole 3 8/13/2010 Carbozole 3 8/13/2010 Carbozole 3 8/13/2010 3,3'-Dimethylbenzidine 1 8/13/2010 Coronene 1 8/13/2010 Coronene 1 8/13/2010 Coronene 1 8/13/2010 Coronene 2 8/13/2010 Coronene 2 8/13/2010 Coronene 2 8/13/2010 Coronene 2 8/13/2010 Coronene 3 8/13/2010Coronene 3 8/13/2010

Coronene 3 8/13/2010 Coronene 3 8/13/2010 1,2-Diphenylhydrazine 1 8/13/2010 Dibenzo(a,e)pyrene 1 8/13/2010 Dibenzo(a,e)pyrene 1 8/13/2010 Dibenzo(a,e)pyrene 1 8/13/2010 Dibenzo(a,e)pyrene 2 8/13/2010 Dibenzo(a,e)pyrene 2 8/13/2010 Dibenzo(a,e)pyrene 2 8/13/2010 Dibenzo(a,e)pyrene 2 8/13/2010 Dibenzo(a,e)pyrene 3 8/13/2010 Dibenzo(a,e)pyrene 3 8/13/2010 Dibenzo(a,e)pyrene 3 8/13/2010 Dibenzo(a,e)pyrene 3 8/13/2010 m-Terphenyl 1 8/13/2010 m-Terphenyl 1 8/13/2010 m-Terphenyl 1 8/13/2010 m-Terphenyl 1 8/13/2010 m-Terphenyl 2 8/13/2010 m-Terphenyl 2 8/13/2010 m-Terphenyl 2 8/13/2010 m-Terphenyl 2 8/13/2010 m-Terphenyl 3 8/13/2010 m-Terphenyl 3 8/13/2010 m-Terphenyl 3 8/13/2010 m-Terphenyl 3 8/13/2010 N-Nitrosodimethylam ine 1 8/13/2010 N-Nitrosodimethylam ine 1 8/13/2010 N-Nitrosodimethylam ine 1 8/13/2010 N-Nitrosodimethylam ine 1 8/13/2010 N-Nitrosodimethylam ine 2 8/13/2010 N-Nitrosodimethylam ine 2 8/13/2010 N-Nitrosodimethylam ine 2 8/13/2010 N-Nitrosodimethylam ine 2 8/13/2010 N-Nitrosodimethylam ine 3 8/13/2010 N-Nitrosodimethylam ine 3 8/13/2010 N-Nitrosodimethylam ine 3 8/13/2010 N-Nitrosodimethylam ine 3 8/13/2010 Pentachlorophenol 1 8/13/2010 Pentachlorophenol 1 8/13/2010 Pentachlorophenol 1 8/13/2010 Pentachlorophenol 1 8/13/2010 Pentachlorophenol 2 8/13/2010 Pentachlorophenol 2 8/13/2010 Pentachlorophenol 2 8/13/2010 Pentachlorophenol 2 8/13/2010 Pentachlorophenol 3 8/13/2010 Pentachlorophenol 3 8/13/2010 Pentachlorophenol 3 8/13/2010 Pentachlorophenol 3 8/13/2010 N-Nitrosodiphenylam ine 1 8/13/2010N-Nitrosodiphenylam ine 1 8/13/2010

N-Nitrosodiphenylam ine 1 8/13/2010 N-Nitrosodiphenylam ine 1 8/13/2010 N-Nitrosodiphenylam ine 2 8/13/2010 N-Nitrosodiphenylam ine 2 8/13/2010 N-Nitrosodiphenylam ine 2 8/13/2010 N-Nitrosodiphenylam ine 2 8/13/2010 N-Nitrosodiphenylam ine 3 8/13/2010 N-Nitrosodiphenylam ine 3 8/13/2010 N-Nitrosodiphenylam ine 3 8/13/2010 N-Nitrosodiphenylam ine 3 8/13/2010 Phenol 1 8/13/2010 Phenol 1 8/13/2010 Phenol 1 8/13/2010 Phenol 1 8/13/2010 Phenol 2 8/13/2010 Phenol 2 8/13/2010 Phenol 2 8/13/2010 Phenol 2 8/13/2010 Phenol 3 8/13/2010 Phenol 3 8/13/2010 Phenol 3 8/13/2010 Phenol 3 8/13/2010 o-Terphenyl 1 8/13/2010 o-Terphenyl 1 8/13/2010 o-Terphenyl 1 8/13/2010 o-Terphenyl 1 8/13/2010 o-Terphenyl 2 8/13/2010 o-Terphenyl 2 8/13/2010 o-Terphenyl 2 8/13/2010 o-Terphenyl 2 8/13/2010 o-Terphenyl 3 8/13/2010 o-Terphenyl 3 8/13/2010 o-Terphenyl 3 8/13/2010 o-Terphenyl 3 8/13/2010 Perylene 1 8/13/2010 Perylene 1 8/13/2010 Perylene 1 8/13/2010 Perylene 1 8/13/2010 Perylene 2 8/13/2010 Perylene 2 8/13/2010 Perylene 2 8/13/2010 Perylene 2 8/13/2010 Perylene 3 8/13/2010 Perylene 3 8/13/2010 Perylene 3 8/13/2010 Perylene 3 8/13/2010 p-Terphenyl 1 8/13/2010 p-Terphenyl 1 8/13/2010 p-Terphenyl 1 8/13/2010 p-Terphenyl 1 8/13/2010 p-Terphenyl 2 8/13/2010p-Terphenyl 2 8/13/2010

p-Terphenyl 2 8/13/2010 p-Terphenyl 2 8/13/2010 p-Terphenyl 3 8/13/2010 p-Terphenyl 3 8/13/2010 p-Terphenyl 3 8/13/2010 p-Terphenyl 3 8/13/2010 Quinoline 1 8/13/2010 Quinoline 1 8/13/2010 Quinoline 1 8/13/2010 Quinoline 1 8/13/2010 Quinoline 2 8/13/2010 Quinoline 2 8/13/2010 Quinoline 2 8/13/2010 Quinoline 2 8/13/2010 Quinoline 3 8/13/2010 Quinoline 3 8/13/2010 Quinoline 3 8/13/2010 Quinoline 3 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 1 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 2 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 1,2,4-Trichlorobenzene 3 8/13/2010 2,4,5-Trichlorophenol 1 8/13/2010 2,4,5-Trichlorophenol 1 8/13/2010 2,4,5-Trichlorophenol 1 8/13/2010 2,4,5-Trichlorophenol 1 8/13/2010 2,4,5-Trichlorophenol 2 8/13/2010 2,4,5-Trichlorophenol 2 8/13/2010 2,4,5-Trichlorophenol 2 8/13/2010 2,4,5-Trichlorophenol 2 8/13/2010 2,4,5-Trichlorophenol 3 8/13/2010 2,4,5-Trichlorophenol 3 8/13/2010 2,4,5-Trichlorophenol 3 8/13/2010 2,4,5-Trichlorophenol 3 8/13/2010 2,4,6-Trichlorophenol 1 8/13/2010 2,4,6-Trichlorophenol 1 8/13/2010 2,4,6-Trichlorophenol 1 8/13/2010 2,4,6-Trichlorophenol 1 8/13/2010 2,4,6-Trichlorophenol 2 8/13/2010 2,4,6-Trichlorophenol 2 8/13/2010 2,4,6-Trichlorophenol 2 8/13/2010 2,4,6-Trichlorophenol 2 8/13/2010 2,4,6-Trichlorophenol 3 8/13/20102,4,6-Trichlorophenol 3 8/13/2010

2,4,6-Trichlorophenol 3 8/13/2010 2,4,6-Trichlorophenol 3 8/13/2010 Tetralin 1 8/13/2010 Tetralin 1 8/13/2010 Tetralin 1 8/13/2010 Tetralin 1 8/13/2010 Tetralin 2 8/13/2010 Tetralin 2 8/13/2010 Tetralin 2 8/13/2010 Tetralin 2 8/13/2010 Tetralin 3 8/13/2010 Tetralin 3 8/13/2010 Tetralin 3 8/13/2010 Tetralin 3 8/13/2010Note: Each run should include a value for each fraction and the total for each pollutant.

10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 Test Start Time Test End Date Test End Time15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:4710:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:4715:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:4710:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:4715:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:4710:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:4715:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:4710:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:4715:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:4710:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:4715:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:4710:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:4715:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:5318:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 10:15 8/13/2010 12:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 15:03 8/13/2010 17:47 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53 18:27 8/13/2010 20:53Footnotes: * Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses ** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses *** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses

Fraction Measured Value (μg/m3) Basis (Wet or Dry)

Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.69] Dry Front Half Composite* [<0.91] Dry Back Half Composite** [<0.91] Dry Condensate Composite*** [<0.91] Dry Total Composite [<2.72] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.70] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] DryBack Half Composite** [<0.07] Dry

Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] DryBack Half Composite** [<2.70] Dry

Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] DryBack Half Composite** [<0.07] Dry

Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.13] Dry Back Half Composite** 0.16 Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.43] Dry Front Half Composite* [<0.14] Dry Back Half Composite** 0.19 Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.46] Dry Front Half Composite* [<0.13] Dry Back Half Composite** 0.18 Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.44] Dry Front Half Composite* [<0.07] Dry Back Half Composite** 0.09 Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.23] Dry Front Half Composite* [<0.07] Dry Back Half Composite** 0.14 Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.28] Dry Front Half Composite* [<0.07] Dry Back Half Composite** 0.09 Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.22] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] DryBack Half Composite** [<0.07] Dry

Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.07] Dry Back Half Composite** [<0.07] Dry Condensate Composite*** [<0.07] Dry Total Composite [<0.20] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] DryBack Half Composite** [<8.99] Dry

Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<1.80] Dry Back Half Composite** [<1.80] Dry Condensate Composite*** [<1.80] Dry Total Composite [<5.39] Dry Front Half Composite* [<1.81] Dry Back Half Composite** [<1.81] Dry Condensate Composite*** [<1.81] Dry Total Composite [<5.44] Dry Front Half Composite* [<1.80] Dry Back Half Composite** [<1.80] Dry Condensate Composite*** [<1.80] Dry Total Composite [<5.39] Dry Front Half Composite* [<2.24] Dry Back Half Composite** [<2.24] Dry Condensate Composite*** [<2.24] Dry Total Composite [<6.73] Dry Front Half Composite* [<2.27] Dry Back Half Composite** [<2.27] Dry Condensate Composite*** [<2.27] Dry Total Composite [<6.80] Dry Front Half Composite* [<2.25] Dry Back Half Composite** [<2.25] Dry Condensate Composite*** [<2.25] Dry Total Composite [<6.74] Dry Front Half Composite* [<2.24] Dry Back Half Composite** [<2.24] Dry Condensate Composite*** [<2.24] Dry Total Composite [<6.73] Dry Front Half Composite* [<2.27] Dry Back Half Composite** [<2.27] Dry Condensate Composite*** [<2.27] Dry Total Composite [<6.80] Dry Front Half Composite* [<2.25] Dry Back Half Composite** [<2.25] Dry Condensate Composite*** [<2.25] Dry Total Composite [<6.74] Dry Front Half Composite* 7.63 DryBack Half Composite** [<3.59] Dry

Condensate Composite*** [<3.59] Dry Total Composite [<14.81] Dry Front Half Composite* [<3.63] Dry Back Half Composite** [<3.63] Dry Condensate Composite*** [<3.63] Dry Total Composite [<10.88] Dry Front Half Composite* [<3.60] Dry Back Half Composite** [<3.60] Dry Condensate Composite*** [<3.60] Dry Total Composite [<10.79] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.69] Dry Front Half Composite* [<0.91] Dry Back Half Composite** [<0.91] Dry Condensate Composite*** [<0.91] Dry Total Composite [<2.72] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.70] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.69] Dry Front Half Composite* [<0.91] Dry Back Half Composite** [<0.91] Dry Condensate Composite*** [<0.91] Dry Total Composite [<2.72] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.70] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] Dry Back Half Composite** [<8.99] Dry Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<2.24] Dry Back Half Composite** [<2.24] Dry Condensate Composite*** [<2.24] Dry Total Composite [<6.73] Dry Front Half Composite* [<2.27] DryBack Half Composite** [<2.27] Dry

Condensate Composite*** [<2.27] Dry Total Composite [<6.80] Dry Front Half Composite* [<2.25] Dry Back Half Composite** [<2.25] Dry Condensate Composite*** [<2.25] Dry Total Composite [<6.74] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<3.59] Dry Back Half Composite** [<3.59] Dry Condensate Composite*** [<3.59] Dry Total Composite [<10.77] Dry Front Half Composite* [<3.63] Dry Back Half Composite** [<3.63] Dry Condensate Composite*** [<3.63] Dry Total Composite [<10.88] Dry Front Half Composite* [<3.60] Dry Back Half Composite** [<3.60] Dry Condensate Composite*** [<3.60] Dry Total Composite [<10.79] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.04] Dry Front Half Composite* [<1.36] Dry Back Half Composite** [<1.36] Dry Condensate Composite*** [<1.36] Dry Total Composite [<4.08] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.05] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] DryBack Half Composite** [<8.99] Dry

Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.04] Dry Front Half Composite* [<1.36] Dry Back Half Composite** [<1.36] Dry Condensate Composite*** [<1.36] Dry Total Composite [<4.08] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.05] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<1.80] DryBack Half Composite** [<1.80] Dry

Condensate Composite*** [<1.80] Dry Total Composite [<5.39] Dry Front Half Composite* [<1.81] Dry Back Half Composite** [<1.81] Dry Condensate Composite*** [<1.81] Dry Total Composite [<5.44] Dry Front Half Composite* [<1.80] Dry Back Half Composite** [<1.80] Dry Condensate Composite*** [<1.80] Dry Total Composite [<5.39] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<1.35] Dry Back Half Composite** 2.69 Dry Condensate Composite*** [<1.35] Dry Total Composite [<5.39] Dry Front Half Composite* [<1.36] Dry Back Half Composite** [<1.36] Dry Condensate Composite*** [<1.36] Dry Total Composite [<4.08] Dry Front Half Composite* [<1.35] Dry Back Half Composite** 4.49 Dry Condensate Composite*** [<1.35] Dry Total Composite [<7.19] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.04] Dry Front Half Composite* [<1.36] Dry Back Half Composite** [<1.36] Dry Condensate Composite*** [<1.36] Dry Total Composite [<4.08] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.05] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.46] Dry Front Half Composite* [<4.53] DryBack Half Composite** [<4.53] Dry

Condensate Composite*** [<4.53] Dry Total Composite [<13.60] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.48] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.69] Dry Front Half Composite* [<0.91] Dry Back Half Composite** [<0.91] Dry Condensate Composite*** [<0.91] Dry Total Composite [<2.72] Dry Front Half Composite* [<0.90] Dry Back Half Composite** [<0.90] Dry Condensate Composite*** [<0.90] Dry Total Composite [<2.70] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.04] Dry Front Half Composite* [<1.36] Dry Back Half Composite** [<1.36] Dry Condensate Composite*** [<1.36] Dry Total Composite [<4.08] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.05] Dry Front Half Composite* [<3.59] Dry Back Half Composite** [<3.59] Dry Condensate Composite*** [<3.59] Dry Total Composite [<10.77] Dry Front Half Composite* [<3.63] Dry Back Half Composite** [<3.63] Dry Condensate Composite*** [<3.63] Dry Total Composite [<10.88] Dry Front Half Composite* [<3.60] Dry Back Half Composite** [<3.60] Dry Condensate Composite*** [<3.60] Dry Total Composite [<10.79] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] DryBack Half Composite** [<0.27] Dry

Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.04] Dry Front Half Composite* [<1.36] Dry Back Half Composite** [<1.36] Dry Condensate Composite*** [<1.36] Dry Total Composite [<4.08] Dry Front Half Composite* [<1.35] Dry Back Half Composite** [<1.35] Dry Condensate Composite*** [<1.35] Dry Total Composite [<4.05] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.46] Dry Front Half Composite* [<4.53] Dry Back Half Composite** [<4.53] Dry Condensate Composite*** [<4.53] Dry Total Composite [<13.60] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.48] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.69] DryBack Half Composite** [<2.69] Dry

Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.46] Dry Front Half Composite* [<4.53] Dry Back Half Composite** [<4.53] Dry Condensate Composite*** [<4.53] Dry Total Composite [<13.60] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.48] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] DryBack Half Composite** [<0.27] Dry

Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<26.93] Dry Back Half Composite** [<26.93] Dry Condensate Composite*** [<26.93] Dry Total Composite [<80.79] Dry Front Half Composite* [<27.21] Dry Back Half Composite** [<27.21] Dry Condensate Composite*** [<27.21] Dry Total Composite [<81.62] Dry Front Half Composite* [<26.97] Dry Back Half Composite** [<26.97] Dry Condensate Composite*** [<26.97] Dry Total Composite [<80.91] Dry Front Half Composite* [<4.04] Dry Back Half Composite** [<4.04] Dry Condensate Composite*** [<4.04] Dry Total Composite [<12.12] Dry Front Half Composite* [<4.08] Dry Back Half Composite** [<4.08] Dry Condensate Composite*** [<4.08] Dry Total Composite [<12.24] Dry Front Half Composite* [<4.05] Dry Back Half Composite** [<4.05] Dry Condensate Composite*** [<4.05] Dry Total Composite [<12.14] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.46] Dry Front Half Composite* [<4.53] Dry Back Half Composite** [<4.53] Dry Condensate Composite*** [<4.53] Dry Total Composite [<13.60] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.48] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] DryBack Half Composite** [<0.27] Dry

Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] Dry Back Half Composite** [<8.99] Dry Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] Dry Back Half Composite** [<8.99] Dry Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] Dry Back Half Composite** [<8.99] Dry Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<2.69] DryBack Half Composite** [<2.69] Dry

Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.24] Dry Back Half Composite** [<2.24] Dry Condensate Composite*** [<2.24] Dry Total Composite [<6.73] Dry Front Half Composite* [<2.27] Dry Back Half Composite** [<2.27] Dry Condensate Composite*** [<2.27] Dry Total Composite [<6.80] Dry Front Half Composite* [<2.25] Dry Back Half Composite** [<2.25] Dry Condensate Composite*** [<2.25] Dry Total Composite [<6.74] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.46] Dry Front Half Composite* [<4.53] Dry Back Half Composite** [<4.53] Dry Condensate Composite*** [<4.53] Dry Total Composite [<13.60] Dry Front Half Composite* [<4.49] Dry Back Half Composite** [<4.49] Dry Condensate Composite*** [<4.49] Dry Total Composite [<13.48] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<4.49] Dry Back Half Composite** 73.16 Dry Condensate Composite*** [<4.49] Dry Total Composite [<82.13] Dry Front Half Composite* [<4.53] DryBack Half Composite** 93.41 Dry

Condensate Composite*** [<4.53] Dry Total Composite [<102.47] Dry Front Half Composite* [<4.49] Dry Back Half Composite** 120.91 Dry Condensate Composite*** [<4.49] Dry Total Composite [<129.90] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<8.98] Dry Back Half Composite** [<8.98] Dry Condensate Composite*** [<8.98] Dry Total Composite [<26.93] Dry Front Half Composite* [<9.07] Dry Back Half Composite** [<9.07] Dry Condensate Composite*** [<9.07] Dry Total Composite [<27.21] Dry Front Half Composite* [<8.99] Dry Back Half Composite** [<8.99] Dry Condensate Composite*** [<8.99] Dry Total Composite [<26.97] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] DryBack Half Composite** [<0.27] Dry

Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<13.46] Dry Back Half Composite** [<13.46] Dry Condensate Composite*** [<13.46] Dry Total Composite [<40.39] Dry Front Half Composite* [<13.60] Dry Back Half Composite** [<13.60] Dry Condensate Composite*** [<13.60] Dry Total Composite [<40.81] Dry Front Half Composite* [<13.48] Dry Back Half Composite** [<13.48] Dry Condensate Composite*** [<13.48] Dry Total Composite [<40.45] Dry Front Half Composite* [<4.04] Dry Back Half Composite** [<4.04] Dry Condensate Composite*** [<4.04] Dry Total Composite [<12.12] Dry Front Half Composite* [<4.08] Dry Back Half Composite** [<4.08] Dry Condensate Composite*** [<4.08] Dry Total Composite [<12.24] Dry Front Half Composite* [<4.05] Dry Back Half Composite** [<4.05] Dry Condensate Composite*** [<4.05] Dry Total Composite [<12.14] Dry Front Half Composite* [<2.69] DryBack Half Composite** [<2.69] Dry

Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.24] Dry Back Half Composite** [<2.24] Dry Condensate Composite*** [<2.24] Dry Total Composite [<6.73] Dry Front Half Composite* [<2.27] Dry Back Half Composite** [<2.27] Dry Condensate Composite*** [<2.27] Dry Total Composite [<6.80] Dry Front Half Composite* [<2.25] Dry Back Half Composite** [<2.25] Dry Condensate Composite*** [<2.25] Dry Total Composite [<6.74] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] DryBack Half Composite** [<0.14] Dry

Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.82] Dry Front Half Composite* [<0.27] Dry Back Half Composite** [<0.27] Dry Condensate Composite*** [<0.27] Dry Total Composite [<0.81] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.69] Dry Back Half Composite** [<2.69] Dry Condensate Composite*** [<2.69] Dry Total Composite [<8.08] Dry Front Half Composite* [<2.72] Dry Back Half Composite** [<2.72] Dry Condensate Composite*** [<2.72] Dry Total Composite [<8.16] Dry Front Half Composite* [<2.70] Dry Back Half Composite** [<2.70] Dry Condensate Composite*** [<2.70] Dry Total Composite [<8.09] Dry Front Half Composite* [<2.24] Dry Back Half Composite** [<2.24] Dry Condensate Composite*** [<2.24] Dry Total Composite [<6.73] Dry Front Half Composite* [<2.27] Dry Back Half Composite** [<2.27] Dry Condensate Composite*** [<2.27] Dry Total Composite [<6.80] Dry Front Half Composite* [<2.25] DryBack Half Composite** [<2.25] Dry

Condensate Composite*** [<2.25] Dry Total Composite [<6.74] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry Front Half Composite* [<0.14] Dry Back Half Composite** [<0.14] Dry Condensate Composite*** [<0.14] Dry Total Composite [<0.41] Dry Front Half Composite* [<0.13] Dry Back Half Composite** [<0.13] Dry Condensate Composite*** [<0.13] Dry Total Composite [<0.40] Dry* Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses ** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses *** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses

Test Method Used Data Flag (ADL, BDL, DDL)

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL Semi-Volatile Organic HAP Emission Test ResultsU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD LU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D AD L

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D AD L U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D DLL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLU.S. EPA Method 0010 with SW-846 Method 8270D BDL

U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDL U.S. EPA Method 0010 with SW-846 Method 8270D BDLTest Method

Comments lb/mmBtu μg/dscm @ 7% O2

For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.66E-07 0.18 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.43E-07] [<0.47] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.99E-07 0.21 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.82E-07] [<0.51] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.85E-07 0.19 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.71E-07] [<0.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.69E-08 0.10 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.35E-07] [<0.25] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.47E-07 0.15 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.88E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.04E-08 0.09 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.33E-07] [<0.24] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-08] [<0.07] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.08E-07] [<0.22] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-08] [<0.07] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.13E-07] [<0.22] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-08] [<0.07] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.14E-07] [<0.22] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.85E-06] [<1.97] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.85E-06] [<1.97] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.85E-06] [<1.97] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.54E-06] [<5.90] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.89E-06] [<2.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.89E-06] [<2.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.89E-06] [<2.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.67E-06] [<6.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06] [<2.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06] [<2.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06] [<2.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.71E-06] [<5.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-06] [<7.38] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-06] [<7.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-06] [<7.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-06] [<7.38] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-06] [<7.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-06] [<7.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 7.85E-06 8.36 939 1471For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.52E-05] [<16.24] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.13E-05] [<12.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.14E-05] [<11.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-06] [<7.38] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-06] [<7.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-06] [<7.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.11E-05] [<11.81] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.13E-05] [<12.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.14E-05] [<11.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.85E-06] [<1.97] 939 1471For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.85E-06] [<1.97] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.85E-06] [<1.97] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.54E-06] [<5.90] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.89E-06] [<2.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.89E-06] [<2.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.89E-06] [<2.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.67E-06] [<6.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06] [<2.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06] [<2.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.90E-06] [<2.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.71E-06] [<5.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 2.77E-06 2.95 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<5.54E-06] [<5.90] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 4.76E-06 4.99 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.61E-06] [<7.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-07] [<0.98] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-07] [<1.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-07] [<1.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.69E-06] [<3.94] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.11E-05] [<11.81] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.78E-06] [<4.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.13E-05] [<12.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<3.80E-06] [<4.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.14E-05] [<11.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-06] [<1.48] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-06] [<1.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-06] [<1.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-05] [<88.56] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-05] [<89.97] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-05] [<89.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-05] [<13.28] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.28E-05] [<13.49] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.28E-05] [<13.48] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-06] [<7.38] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-06] [<7.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-06] [<7.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 7.52E-05 80.20 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.62E-06] [<4.92] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.45E-05] [<90.04] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 9.74E-05 102.96 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.73E-06] [<5.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.07E-04] [<112.96] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. 1.28E-04 134.35 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.76E-06] [<4.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.37E-04] [<144.34] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.23E-06] [<9.84] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-05] [<29.52] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.45E-06] [<10.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-05] [<29.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<9.51E-06] [<9.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-05] [<29.97] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-05] [<14.76] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-05] [<44.28] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-05] [<14.99] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-05] [<44.98] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-05] [<14.98] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-05] [<44.95] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-06] [<4.43] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.25E-05] [<13.28] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-06] [<4.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.28E-05] [<13.49] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-06] [<4.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.28E-05] [<13.48] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-06] [<7.38] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-06] [<7.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-06] [<7.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-07] [<0.30] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-07] [<0.89] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-07] [<0.30] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-07] [<0.90] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-07] [<0.30] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-07] [<0.90] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.77E-06] [<2.95] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.31E-06] [<8.86] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.84E-06] [<3.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.51E-06] [<9.00] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.85E-06] [<3.00] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<8.56E-06] [<8.99] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.31E-06] [<2.46] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<6.92E-06] [<7.38] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.36E-06] [<2.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.09E-06] [<7.50] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<2.38E-06] [<2.50] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<7.13E-06] [<7.49] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.38E-07] [<0.15] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.15E-07] [<0.44] 939 1471 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.42E-07] [<0.15] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.25E-07] [<0.45] 935 1452 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<1.43E-07] [<0.15] 933 1446 For M0010 we are reporting to a RDL. Lab RDL = The RDL is generally 5 to 10 times the MDL or equal to the lowest standard of the calibration curve but may be higher or lower in order to comply with specific client or regulatory requirements. It is not necessarily a fixed multiple of the MDL. Lab MDL = Student t factor multiplied by std. deviation of at least 8 replicate analyses of a matrix spike containing the analyte of interest at a level <10 times the desired reporting limit. [<4.28E-07] [<0.45] 933 1446Fuel Input Rate Fuel Type Units of Measure 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #17.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day

7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day

7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day

7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day

7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day

7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day

7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day

7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day

7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.4 11.20 8.22 368,595 285.3 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.2 11.13 8.29 367,737 287.1 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/day 7.3 11.03 8.39 368,102 288.9 1260 bitum inous ton/dayMeasurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type

Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Fuel #2 Fuel #3Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherOther 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

Other Other 0.234 No.2 Fuel Oil (distillate) gallon/m inute

OtherUnits of

Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Fuel #3Other Supporting InformationEIA

Facility Code Facility Name Boiler ID

3152 Sunbury

Generation LP 4

1 8/13/2010 9:27 8/13/2010 2 8/13/2010 13:46 8/13/2010 3 8/13/2010 18:59 8/13/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used

12:49 0.80 Dry U.S. EPA Method 320 18:11 0.80 Dry U.S. EPA Method 320 21:59 0.80 Dry U.S. EPA Method 320 Hydrogen Cyanide Emission Test Results Test End TimeData Flag (ADL,

BDL, DDL) Test Method

Comments ADL 9.30E-04 940 1472 7.4 10.5 ADL 9.30E-04 936 1449 7.2 10.4 ADL 9.40E-04 929 1442 7.3 10.3 Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate 8.2 368595 285.3 1260 bitum inous ton/day Other 0.234 8.3 367737 287.1 1260 bitum inous ton/day Other 0.234 8.4 368102 288.9 1260 bitum inous ton/day Other 0.234 Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas O2(%)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate No.2 Fuel Oil (distillate)

gallon/m inute

Other No.2 Fuel Oil (distillate)

gallon/m inute

Other No.2 Fuel Oil (distillate)

gallon/m inute

Other Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID

3152 Sunbury

Generation LP 4

1 8/13/2010 9:27 8/13/2010 2 8/13/2010 13:46 8/13/2010 3 8/13/2010 18:59 8/13/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used

12:49 32.7 Dry U.S. EPA Method 320 18:11 32.7 Dry U.S. EPA Method 320 21:59 32.7 Dry U.S. EPA Method 320 Test End Time Hydrogen Chloride Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments ADL 0.051 940 1472 7.4 10.5 ADL 0.052 936 1449 7.2 10.4 ADL 0.052 929 1442 7.3 10.3 Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO2(%) Hydrogen Chloride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate 8.2 368595 285.3 1260 bitum inous ton/day Other 0.234 8.3 367737 287.1 1260 bitum inous ton/day Other 0.234 8.4 368102 288.9 1260 bitum inous ton/day Other 0.234 Flue Gas Temperature (F) Fuel #1 Flue Gas O2(%) Flue Gas

Flow Rate (dscfm)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate No.2 Fuel Oil (distillate)

gallon/m inute

Other No.2 Fuel Oil (distillate)

gallon/m inute

Other No.2 Fuel Oil (distillate)

gallon/m inute

Other Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID

3152 Sunbury

Generation LP 4

1 8/13/2010 9:27 8/13/2010 2 8/13/2010 13:46 8/13/2010 3 8/13/2010 18:59 8/13/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used

12:49 15.8 Dry U.S. EPA Method 320 18:11 15.8 Dry U.S. EPA Method 320 21:59 15.8 Dry U.S. EPA Method 320 Hydrogen Flouride Emission Test Results Test End TimeData Flag (ADL,

BDL, DDL) Test Method

Comments ADL 0.014 940 1472 7.4 ADL 0.014 936 1449 7.2 ADL 0.014 929 1442 7.3 Hydrogen Flouride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method 10.5 8.2 368595 285.3 1260 bitum inous ton/day Other 10.4 8.3 367737 287.1 1260 bitum inous ton/day Other 10.3 8.4 368102 288.9 1260 bitum inous ton/day Other

Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas CO2(%) Flue Gas

O2(%)Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method 0.234 No.2 Fuel Oil (distillate)

gallon/m inute

Other 0.234 No.2 Fuel Oil (distillate)

gallon/m inute

Other 0.234 No.2 Fuel Oil (distillate)

gallon/m inute

Other Fuel #2 Fuel #3Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

Run Number Test Start Date Test Start TimeMeasured NO (ppm) Test End Time Test End DateMeasured NO2(ppm) Basis (Wet or Dry) Test Method Used NOXEmission Test ResultsData Flag (ADL, BDL, DDL) Test Method Comments (lb/mmBtu) Total NOXCalculated Emission Rateppmdv @ 7% O2 Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 3152 Sunbury

Generation LP 4

Run Number Test Start Date Test Start TimeTotal Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter) Test End Time Test End DateTest Method Used Data Flag (ADL, BDL, DDL) Constisuent Emission Test ResultsTest Method Comments Fuel Input Rate Flue Gas Temperat ure (F) Flue Gas Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel #1 Fuel #2Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel #3 Fuel #4Other Supporting Information