### Instructions for completing the Fuel Material Analysis Information

This Information Collection Request (ICR) spreadsheet is intended to collect information about chemical analyses of fuels used fossil fuel burning power plants. Constituents of concern are: mercury, chlorine, fluorine, and metals, such as antimony, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, and selenium. This spreadsheet is intended to be used for one boiler of one facility but is designed to allow multiple (up to 4) fuel analyses at that specific boiler. Th number of analyses would coincide with one boiler where emissions testing for all 4 HAP surrogates were being tested. Data for multiple boilers should be handled by using separate spreadsheets. Fields that are highlighted in yellow are required fields. Green highlighted cells should be filled using the drop

- down boxes, included. Gray fields are automatically filled from other fields.

Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_Fuels_Testing.xls (example: 8100_Unit_2_Fuels_Testing.xls).

Please refer to the following steps when using these spreadsheets.
1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the test date on the Boiler Information worksheet. 3. Please choose the type of fuel being sampled using the drop

- down in the fuel column of the Boiler Information worksheet. If you choose "other", please provide a description of the fuel in the Other Fuel Description column. 4. Please provide the analysis method for each constituent in the Analysis Methods worksheet. For example: "ASTM D5865 04". 5. Please check the Units of Measure tables for HHV, Metals, and Cl/Fl in the Picklist worksheet (orange tab). If the units
measure that you plan to report are not found in the Units of measure table, please fill them in the blank, orange highlighted, cell in each table. This allows you to choose the units of measure in the Fuels Sample Results worksheet. 6. Select the HAPs Test Group (i.e., HAP surrogate) for which the tab's data reflects (o range highlighted cell) 7. Provide the Sample Number and Sample Date on the Fuels Sample Results worksheet. You must provide a minimum of 3 composite samples consisting of 3 combined grab samples each, but you are not limited to that number if you have collected
more. 8. Provide the results of the analyses for each constituent requested. Use the drop

- down boxes to fill in the units of
measure.

### Information
This Information Collection Request (ICR) spreadsheet is intended to collect information about chemical analyses of fuels used fossil fuel burning power plants. Constituents of concern are: mercury, chlorine, fluorine, and metals, such as antimony, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, and selenium. This spreadsheet is intended to be used for one boiler of one facility but is designed to allow multiple (up to 4) fuel analyses at that specific boiler. Th is number of analyses would coincide with one boiler where emissions testing for all 4 HAP surrogates were being tested. Fields that are highlighted in yellow are down boxes, included. Gray fields are automatically

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

down in the fuel column of the Boiler Information worksheet. If you choose "other", please provide a description of the fuel in the Other Fuel Description column. 4. Please provide the analysis method for each constituent in the Analysis Methods worksheet. For example: "ASTM D5865

- 5. Please check the Units of Measure tables for HHV, Metals, and Cl/Fl in the Picklist worksheet (orange tab). If the units of
measure that you plan to report are not found in the Units of measure table, please fill them in the blank, orange highlighted, cell in each table. This allows you to choose the units of measure in the Fuels Sample Results worksheet. range highlighted cell)

. 7. Provide the Sample Number and Sample Date on the Fuels Sample Results worksheet. You must provide a minimum of 3 composite samples consisting of 3 combined grab samples each, but you are not limited to that number if you have collected

down boxes to fill in the units ofEIA

Facility Code Facility Name Boiler ID Fuel Type 1

1507 Wi lliam F W ym an 1 

### No.6 Fuel Oil (residual or bunker C)Fuel Type 2 Fuel Type 3 Other Fuel Description 

### No.6 Fuel Oil (residual or bunker C)EIA

Facility Code Facility Name Boiler ID Basis An alyte



### 1507 William F Wyman 1 As Received Higher Heating Value 

### 1507 William F Wyman 1 As Received % Moisture 

### 1507 William F Wyman 1 As Received % Ash 

### 1507 William F Wyman 1 As Received % Sulfur 

### 1507 William F Wyman 1 Dry basis Higher Heating Value 

### 1507 William F Wyman 1 Dry basis % Ash 

### 1507 William F Wyman 1 Dry basis % Sulfur 

### 1507 William F Wyman 1 Dry basis Antim ony 

### 1507 William F Wyman 1 Dry basis Arsenic 

### 1507 William F Wyman 1 Dry basis Bery llium 

### 1507 William F Wyman 1 Dry basis Cadmium 

### 1507 William F Wyman 1 Dry basis Chlorine 

### 1507 William F Wyman 1 Dry basis Chromium 

### 1507 William F Wyman 1 Dry basis Cobalt 

### 1507 William F Wyman 1 Dry basis Fluorine 

### 1507 William F Wyman 1 Dry basis Lead 

### 1507 William F Wyman 1 Dry basis Manganese 

### 1507 William F Wyman 1 Dry basis Mercury 

### 1507 William F Wyman 1 Dry basis Nickel 

### 1507 William F Wyman 1 Dry basis SeleniumAn alysis M ethod for each Analyte

(example: ASTM D5865-04)



### ASTM D4928

ASTM D240-02

ASTM D4239-08 SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010B SW846 6010BEIA

Facility Code Facility

Name Boiler ID HAPs Test Group 

### 1507 William F Wyman 1 Mercury and non-mercury metalic HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 1-03/02/10-F 

### 3/2/2010 3/2/2010 1-03/03/10-F 

### 3/3/2010 3/3/2010 1-03/04/10-F 

### 3/4/2010 3/4/2010 Fuel Testing Results

### Mercury and non-mercury metalic HAPs

% Moisture (as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

### 0.157 18100 0.677 0.272 18200 0.682 0.366 18000 0.685Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 

### [<100] mg/Kg 3.07E-04 mg/Kg 3.3 mg/Kg 0.18 mg/Kg 0.013 207 mg/Kg 3.46E-04 mg/Kg 3.3 mg/Kg 0.17 mg/Kg 0.013 229 mg/Kg 3.07E-04 mg/Kg 3.2 mg/Kg 0.17 mg/Kg 0.014Beryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

### mg/Kg 0.0069 mg/Kg 0.087 mg/Kg 0.18 mg/Kg 1.6 mg/Kg mg/Kg 0.006 mg/Kg 0.089 mg/Kg 0.16 mg/Kg 1.6 mg/Kg mg/Kg 0.0057 mg/Kg 0.084 mg/Kg 0.16 mg/Kg 1.6 mg/KgNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 

### 21.5 mg/Kg [<0.022] mg/Kg [<68] mg/Kg 0.83 mg/Kg 21.2 mg/Kg [<0.017] mg/Kg [<76] mg/Kg 0.81 mg/Kg 20.9 mg/Kg [<0.017] mg/Kg [<71] mg/Kg 0.80 mg/Kg Proximate Analy ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur 

### 87.28 10.35 1.54 0.677 87.19 10.42 1.49 0.682 87.3 10.46 1.28 0.685 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtOxygen



### 0.89 0.56 0.74EIA

Facility Code Facility

Name Boiler ID HAPs Test Group 

### 1507 William F Wyman 1 Acid gas HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating

Value (HHV) (as received) HHV Units 1-03/02/10-F 

### 3/2/2010 3/2/2010 Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

### 0.157 18100 0.677Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 

### [<100] mg/Kg 3.07E-04 mg/Kg 3.3 mg/Kg 0.18 mg/Kg 0.013Beryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

### mg/Kg 0.0069 mg/Kg 0.087 mg/Kg 0.18 mg/Kg 1.6 mg/KgNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units 

### 21.5 mg/Kg [<0.022] mg/Kg [<68] mg/Kg 0.83 mg/KgNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Total Moisture Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur 

### 87.28 10.35 1.54 0.677 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Oxygen 

### 0.89EIA

Facility Code Facility

Name Boiler ID HAPs Test Group 

### 1507 William F Wyman 1 Non-dioxin/furan organic HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date (MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 1-03/02/10-F 

### 3/2/2010 3/2/2010 1-03/03/10-F 

### 3/3/2010 3/3/2010 1-03/04/10-F 

### 3/4/2010 3/4/2010 Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

### 0.157 18100 0.677 0.272 18200 0.682 0.366 18000 0.685Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 

### [<100] mg/Kg 3.07E-04 mg/Kg 3.3 mg/Kg 0.18 mg/Kg 0.013 207 mg/Kg 3.46E-04 mg/Kg 3.3 mg/Kg 0.17 mg/Kg 0.013 229 mg/Kg 3.07E-04 mg/Kg 3.2 mg/Kg 0.17 mg/Kg 0.014Beryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

### mg/Kg 0.0069 mg/Kg 0.087 mg/Kg 0.18 mg/Kg 1.6 mg/Kg mg/Kg 0.006 mg/Kg 0.089 mg/Kg 0.16 mg/Kg 1.6 mg/Kg mg/Kg 0.0057 mg/Kg 0.084 mg/Kg 0.16 mg/Kg 1.6 mg/KgNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 

### 21.5 mg/Kg [<0.022] mg/Kg [<68] mg/Kg 0.83 mg/Kg 21.2 mg/Kg [<0.017] mg/Kg [<76] mg/Kg 0.81 mg/Kg 20.9 mg/Kg [<0.017] mg/Kg [<71] mg/Kg 0.80 mg/Kg Proximate Analy ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen 

### 87.28 10.35 1.54 0.677 0.89 87.19 10.42 1.49 0.682 0.56 87.3 10.46 1.28 0.685 0.74 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtEIA

Facility Code Facility

Name Boiler ID HAPs Test Group 

### 1507 William F Wyman 1 Dioxin/furan HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 1-03/02/10-F 

### 3/2/2010 3/2/2010 1-03/03/10-F 

### 3/3/2010 3/3/2010 1-03/04/10-F 

### 3/4/2010 3/4/2010 Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

### 0.157 18100 0.677 0.272 18200 0.682 0.366 18000 0.685Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 

### [<100] mg/Kg 3.07E-04 mg/Kg 3.3 mg/Kg 0.18 mg/Kg 0.013 207 mg/Kg 3.46E-04 mg/Kg 3.3 mg/Kg 0.17 mg/Kg 0.013 229 mg/Kg 3.07E-04 mg/Kg 3.2 mg/Kg 0.17 mg/Kg 0.014Beryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

### mg/Kg 0.0069 mg/Kg 0.087 mg/Kg 0.18 mg/Kg 1.6 mg/Kg mg/Kg 0.006 mg/Kg 0.089 mg/Kg 0.16 mg/Kg 1.6 mg/Kg mg/Kg 0.0057 mg/Kg 0.084 mg/Kg 0.16 mg/Kg 1.6 mg/KgNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 

### 21.5 mg/Kg [<0.022] mg/Kg [<68] mg/Kg 0.83 mg/Kg 21.2 mg/Kg [<0.017] mg/Kg [<76] mg/Kg 0.81 mg/Kg 20.9 mg/Kg [<0.017] mg/Kg [<71] mg/Kg 0.80 mg/Kg Proximate Analy ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen 

### 87.28 10.35 1.54 0.677 0.89 87.19 10.42 1.49 0.682 0.56 87.3 10.46 1.28 0.685 0.74 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtUnits of Measure Tables: Please do not modify these tables, except to add your own unit of measure to the

Fuel Units of Measure - HHV anthracite Btu/lb bitum inous Btu/gallon subbituminous lignite coal refuse (culm or gob) No.2 Fuel Oil (distillate) No.6 Fuel Oil (residual or bunker C) Units of Measure - Metals sy nfuel mg /g petroleum coke μg/g other mg /KgUnits of Measure Tables: Please do not modify these tables, except to add your own unit of measure to the orangehightlighted cell, if necessary

.

Units of Measure - Cl, Fl % ppm mg /Kg