Name: Lisa Pognon

Title:

Company: Calpine

Sign Date: 8:23:10 AM

Name: Bill Kissel

Title: President

Company: Analytical Testing Consultants, Inc.

Sign Date: 8:23:10 AM

Permitted Facility Representative / Date Testing Company Representative / Date

Conectiv Edgemoor 4

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, March 04, 2011 Page 1 of 7
Conectiv Edgemoor 4

8:23:10 AM

Facility Information:

Conectiv Energy, Edgemoor Unit 4

104 Hay Road

Edgemoor DE 19809

Contact: Mr. Ed Rodichok

Phone:

Fax:

Email:

Testing Company:

Analytical Testing Consultants, Inc.

1630 Dale Earnhardt Blvd

Kannapolis NC 28083

Contact:Mr. Bill Kissel

Phone: 800 733-3193

Fax: 704 932-0570

Email: bkissel@atc-net.net

Air Permit Number: Permitted Source ID/Name:

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Greater than 90%

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Coal, Oil, gas fired Utility Boiler - Edgemoor Unit 4

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack 149.3 0 0 0 2 8 4 12

Friday, March 04, 2011 Page 2 of 7
Conectiv Edgemoor 4

8:23:10 AM

Friday, March 04, 2011 Page 3 of 7
Conectiv Edgemoor 4

8:23:10 AM

Sampling / Stack Data Results Summary

Location Stack - Method 23

Average

Run Number 1 2 3

Test Date 4:20:10 AM 4/21/2010 4/22/2010

Run Start Time

Run Finish Time

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 246.472 267.608 241.610 251.897

Moisture Content of Stack Gas, % 9.18 8.34 9.10 8.873

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 12 12 6.93 10.310

Oxygen, % 6.84 6.88 12 8.573

Average Stack Gas Temperature, °F 263.08 260.42 265.50 263.000

Dry Volumetric Flow Rate, dry scfm 330,896.3 351,128.3 342,375.6 341,466.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 496,467.8 520,248.0 521,196.3 512,637.367

Percent Isokinetic of Sampling Rate, % 96.8 99.1 91.7 95.867

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, March 04, 2011 Page 4 of 7
Conectiv Edgemoor 4

8:23:10 AM

Emissions Summary

Process Run Data

Location: Stack - Method 23

Compound: Total TEQ Dioxans

Average

RunNumber 1 2 3

Mass_mg 0.000000468 0.000000148 0.000000152 0.000

ng/dscm 6.71E-02 1.95E-02 2.22E-02 0.036

ng/dscm@7%O2 6.63E-02 1.93E-02 3.47E-02 0.040

Friday, March 04, 2011 Page 5 of 7
Conectiv Edgemoor 4

8:23:10 AM

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 0 0

1 Unit Load 140 MW 140

1 Heat Input Million Btus/million BTU using O2 0 0

2 0 0

2 Unit Load 140 MW 140

2 Heat Input Million Btus/million BTU using O2 0 0

3 0 0

3 Unit Load 140 MW 140

3 Heat Input Million Btus/million BTU using O2 0 0

Run Name Value UOM Comments

Target

Value

1 ESP 0 0

Friday, March 04, 2011 Page 6 of 7
Conectiv Edgemoor 4

8:23:10 AM

Sampling / Stack Data Results Detail

Location Stack - Method 23

Average

Run Number 1 2 3

Test Date 4:20:10 AM 4/21/2010 4/22/2010

Run Start Time

Run Finish Time

Net Traversing Points 12 12 12

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.189 0.189 0.189 0.189

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.963 0.963 0.963 0.963

Barometric Pressure, inches of Mercury 29.96 29.95 29.6 29.837

Average Orifice Meter Differential, inches H2O 1.04 1.17 1.14 1.117

Dry Gas Meter Volume Sampled, cubic feet 261.145 277.210 254.925 264.427

Average Dry Gas Meter Temperature, °F 80.83 68.75 72.25 73.943

Dry Gas Meter Volume Sampled, dscf 246.472 267.608 241.610 251.897

Total Moisture Liquid collected, g 529 517 514 520.000

Volume of Water Vapor, standard cubic feet 24.90 24.34 24.19 24.477

Moisture Content of Stack Gas, % 9.18 8.34 9.10 8.873

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9082 0.9166 0.909 0.911

Carbon Dioxide, % 12 12 6.93 10.310

Oxygen, % 6.84 6.88 12 8.573

Carbon Monoxide & Nitrogen, % 81.16 81.12 81.07 81.117

Fuel Factor 1.17 1.17 1.28

Dry Molecular Weight, lb/lb-Mole 30.19 30.20 29.59 29.993

Wet Molecular weight, lb/lb-Mole 29.07 29.18 28.54 28.930

Flue Gas Static Pressure, inches of H2O 1.5 1.5 1.5 1.500

Absolute Flue Gas Pressure, inches of Mercury 30.07 30.06 29.71 29.947

Average Stack Gas Temperature, °F 263.08 260.42 265.50 263.000

Average Velocity Head, inches of H2O 1.0857675451

2383

1.200964719

42813

1.157073390

36865

1.148

Average Stack Gas Velocity, feet/second 68.06 71.32 71.45 70.277

Stack Cross-Sectional Area, square feet 121.576 121.576 121.576 121.576

Dry Volumetric Flow Rate, dry scfm 330,896.3 351,128.3 342,375.6 341,466.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 496,467.8 520,248.0 521,196.3 512,637.367

Percent Isokinetic of Sampling Rate, % 96.8 99.1 91.7 95.867

Percent Excess Air, % 46.9 47.3 127.6 73.933

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 149.3 149.3 149.3

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, March 04, 2011 Page 7 of 7