Facility _Information

facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_ty pe

legal_address

legal_city legal_state legal_zip 2168 2168 Associated Electric Cooperative, Inc. Associated Electric Cooperative, Inc.

legal owner2814 South Golden Springfield MO 65801

Page 1Facility _Information

plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Thomas Hill

5693 Hwy

F Clifton Hill MO 65244 Thomas Hill Energy Center5693 Hwy

F Clifton Hill MO 65244

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE TRUE FALSE FALSE TRUE TRUE TRUE FALSE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE TRUE Report within 10 days of eventSSM reporting within 2 days of becoming aware of event - 10 CSR 10-6.050 No Analysis TRI 2008 Annual is a report received annually from the mine and does not represent any one train delivery

.

Page 4Facility _Information

Analysis TRI 2008 Annual is a report received annually from the mine and does not represent any one train delivery

.

Page 5facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 2168 1 Environm ental Coordinator Kim Dickerson

6602613263

6602614211263

kdickerson@aeci.org

TRUE

Page 6facility _coal_utilized

facility _id coal_ty pe percentage_mass percentage_btu

synfuel_ty pe

coal_note 2168 bitum inous 0.1 0.1 2168 subbituminous 99.9 99.9

Page 7facility _oil_utilized

facility _id oil_ty pe percentage_volume percentage_btu

other_type 2168 No.2 Fuel Oil (distillate) 100 100

Page 8facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 2168 Boiler Cleaning Solutions

TRUE TRUE 400 tons/year Yes Boiler cleaning solutionsare not fuels as suggested in the ICR. Rather, the solutions are evaporated in the boiler and the small amount of resulting solid material is captured in the particulate control device. 2168 Used Oil TRUE TRUE 100 tons/year Yes Electric utilities are permitted to burn used oil so long as it classifies as on or off spec used oil and not as a hazardous waste. Only on or off spec oil is combusted in the boilers.

Page 9facility _other_materials

rcra_explain Boiler cleaning solutionsare not fuels as suggested in the ICR. Rather, the solutions are evaporated in the boiler and the small amount of resulting solid material is captured in the particulate control device. Electric utilities are permitted to burn used oil so long as it classifies as on or off spec used oil and not as a hazardous waste. Only on or off spec oil is combusted in the boilers.

Page 10facility _other_materials

Boiler cleaning solutionsare not fuels as suggested in the ICR. Rather, the solutions are evaporated in the boiler and the small amount of resulting solid material is captured in the particulate control device. Electric utilities are permitted to burn used oil so long as it classifies as on or off spec used oil and not as a hazardous waste. Only on or off spec oil is combusted in the boilers.

Page 11boiler_information

facility _id boiler_id boiler_ty pe boiler_other bottom_design

design_fuel heat_input ma x_heat_input MW e_capacity 2168 MB1 Cyclone firing We t Bottom coal 1882 1882 185 2168 MB2 Cyclone firing We t Bottom coal 2970 2970 304 2168 MB3 Wa ll firing - opposed firing Dry Bottom coal 7000 7000 715

Page 12boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 166 88.9 87 1800 1800 1000 1000 FALSE 1000 282 88.3 86.6 2400 2400 1000 1000 FALSE 1000 670 89.3 87.5 2400 2400 1000 1000 FALSE 1000

Page 13boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1000 7226 78.6 N FALSE FALSE 1000 7151 81 N FALSE FALSE 1000 6466 74.6 Subpart D FALSE

Page 14boiler_information

NOx_control

SO2_control

combustion_additives Yes Yes No Yes Yes No Yes Yes No

Page 15boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 2168 MB1 coal - bituminous 2007 0.11 0.11 2168 MB1 coal - bituminous 2008 0.05 0.05 2168 MB1 coal - bituminous 2009 0.03 0.03 2168 MB1 coal - subbituminous 2007 99.8 99.8 2168 MB1 coal - subbituminous 2008 99.75 99.75 2168 MB1 coal - subbituminous 2009 99.8 99.8 2168 MB1 oil - distillate 2007 0.07 0.07 2168 MB1 oil - distillate 2008 0.2 0.2 2168 MB1 oil - distillate 2009 0.17 0.17 2168 MB2 coal - bituminous 2007 0.11 0.11 2168 MB2 coal - bituminous 2008 0.051 0.051 2168 MB2 coal - bituminous 2009 0.03 0.03 2168 MB2 coal - subbituminous 2007 99.82 99.82 2168 MB2 coal - subbituminous 2008 99.756 99.756 2168 MB2 coal - subbituminous 2009 99.8 99.8 2168 MB2 oil - distillate 2007 0.07 0.07 2168 MB2 oil - distillate 2008 0.193 0.193 2168 MB2 oil - distillate 2009 0.17 0.17 2168 MB3 coal - subbituminous 2007 99.9 99.9 2168 MB3 coal - subbituminous 2008 99.9 99.9 2168 MB3 coal - subbituminous 2009 99.9 99.9 2168 MB3 oil - distillate 2007 0.1 0.1 2168 MB3 oil - distillate 2008 0.1 0.1 2168 MB3 oil - distillate 2009 0.1 0.1

Page 16boiler_control_NOx

facility _id boiler_id NOx_ty pe NOx_other NOx_online 2168 MB1 Overfire Air 6/1/2004 2168 MB2 Overfire Air 10/1/2000 2168 MB3 Low NOx Burner 5/1/2006 2168 MB3 Overfire Air 11/1/2002

Page 17boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 2168 MB1 Low Sulfur Coal 2/1/1993 2168 MB1 Low Sulfur Fuel Oil 11/1/1999 2168 MB2 Low Sulfur Coal 2/1/1993 2168 MB2 Low Sulfur Fuel Oil 11/1/1999 2168 MB3 Low Sulfur Coal 2/1/1993 2168 MB3 Low Sulfur Fuel Oil 11/1/1999

Page 18boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 19facility _units

facility _id unit_id 2168 MB1 2168 MB2 2168 MB3

Page 20unit_boilers

facility _id unit_id boiler_id 2168 MB1 MB1 2168 MB2 MB2 2168 MB3 MB3

Page 21facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 2168 3-1 NOx control Selective Cataly

tic Reduction FALSE 1/1/2009 Am mo nia 2168 3-2 NOx control Selective Cataly

tic Reduction FALSE 2/1/2009 Am mo nia 2168 3-3 NOx control Selective Cataly

tic Reduction FALSE 5/1/2009 Am mo nia 2168 6-1 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 12/1/1983 2168 6-2 PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 10/1/1979 2168 6-3 PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1983

Page 22facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive 0 0 0

Page 23facility _sampling_ports

facility _id sampling_port_id 2168 2-1 2168 2-2 2168 2-3 2168 4-1 2168 4-2 2168 4-3 2168 5-1 2168 5-2 2168 5-3 2168 7-1 2168 7-2 2168 7-3 2168 8-1 2168 8-2 2168 8-3

Page 24facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 2168 9-1 411 16.58 48.89 2168 9-2 400 17.17 75.34 2168 9-3 622 30.58 59.79

Page 25configurations

facility _id configuration_id 2168 MB1 2168 MB2 2168 MB3

Page 26configuration_components

facility _id configuration_id

component_id

order component_ty pe port_near 2168 MB1 2-1 2 Sam pling Port next 2168 MB1 3-1 4 NOx control 2168 MB1 4-1 3 Sam pling Port pevious 2168 MB1 5-1 5 Sam pling Port next 2168 MB1 6-1 6 PM control 2168 MB1 7-1 7 Sam pling Port pevious 2168 MB1 8-1 8 Sam pling Port next 2168 MB1 9-1 9 Stack 2168 MB1 MB1 1 Unit 2168 MB2 2-2 2 Sam pling Port next 2168 MB2 3-2 3 NOx control 2168 MB2 4-2 4 Sam pling Port pevious 2168 MB2 5-2 5 Sam pling Port next 2168 MB2 6-2 6 PM control 2168 MB2 7-2 7 Sam pling Port pevious 2168 MB2 8-2 8 Sam pling Port next 2168 MB2 9-2 9 Stack 2168 MB2 MB2 1 Unit 2168 MB3 2-3 2 Sam pling Port next 2168 MB3 3-3 3 NOx control 2168 MB3 4-3 4 Sam pling Port pevious 2168 MB3 5-3 5 Sam pling Port next 2168 MB3 6-3 6 PM control 2168 MB3 7-3 7 Sam pling Port pevious 2168 MB3 8-3 8 Sam pling Port next 2168 MB3 9-3 9 Stack 2168 MB3 MB3 1 Unit

Page 27configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_ty pe_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 2168 MB1 PM (Filterable) Fderal - Title V Operating Permit

0.18 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2168 MB1 opacity State - State Operating Permit 40 percent by

weight 6 minutes 2168 MB1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

8 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2168 MB2 PM (Filterable) Fderal - Title V Operating Permit

0.18 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2168 MB2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

8 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2168 MB2 opacity State - State Operating Permit 40 percent by

weight 6 minutes 2168 MB3 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2168 MB3 opacity State - State Operating Permit 20 percent by

weight 6 minutes 2168 MB3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.8 pound per million British Thermal Unit (lb/MMBtu) 2168 MB3 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu)

Page 28configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method Compliance determined by a 3-hour stack test. CAM Plan Pending: Opacity-to-PM Correlation Continuously

recorded opacity

must remain below 40% for each non-exempt 6-minute period.

Compliance determined by a 3-hour stack test. CAM Plan Pending: Opacity-to-PM correlation

continuously

recorded opacity

must remain below 40% for each non-exempt 6- minute period. Compliance determined by a 3-hour stack test CAM Plan Pending: Opacity-to-PM Correlation Continuously

recorded opacity

must remain below 20% based on one non-exempt 6-min. average. If not, corrective action is needed. Measured in percent - (not percent by weight)> 3 hours 1.2 for coal, 0.8 for fuel oil. Subject to Acid Rain and CAIR. 3 hours 0.15 pound per million British Thermal Unit (lb/MMBtu) 1 hour 0.7 for coal, 0.3 for fuel oil. Subject to Acid Rain and CAIR.

Page 29configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting 0.18 pound per million British Thermal Unit (lb/MMBtu)

No Permit Limit To indicate ESP performance, monitor primary & secondary

voltage, prim ary

& secondary

current, sparking rate, and number of fields on line, weekly .An audible or visual alarm indicates ESP trouble.Inspection of rapper operation, TR set operation, the ash removal system need to be in O&M Plan. During major outages, inspect correct plate electrode alignment, the collection surfaces for fouling, the mechanical condition of the TR sets and the internal structural components.Continuous opacity monitoring Make available the Stack testing records.Maintain records of monitoring or control equipment malfunctions, and corrective actions.Maintain record of annual Method 9 observation and all others.Maintain quarterly records of all opacity

averages.Maintain record of opacity exceedqances and monitor downtime events.Maintain a written copy of all inspections and actions taken as a result.Maintain a spare parts inventory Report no later than 10 days after any exceedance 40 percent by

weight No Permit Limit; percent, not percent-by-weight Continous opacity

monitor.Calibrate, maintain and operate the COMs, with daily calibration Record daily

monitoring calibration check.Record daily highest 6-minute average opacity reading.Maintain COMs records.Maintain records of any opacity or monitoring equipment malfunction.Maintain records of method 9 visual observationsKeep records available for 5 y rs. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. 8 pound per million British Thermal Unit (lb/MMBtu)

No Permit Limit The permittee shall install, calibrate, maintain, and operate a continuous emission monitoring system for measuring sulfur dioxide. Conduct daily calibrations.Conduct RATA per Part 75. Maintain sulfur content of fuel .Record daily monitoring system caibration checks.Keep records for 5 y rs.Maintain records of fuel ty pe, verifying a sulfur content <0.5% for fuel oil.Determine heating value of the fuel oil. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. 0.18 pound per million British Thermal Unit (lb/MMBtu)

No Permit limit To indicate ESP performance, monitor primary & secondary

voltage ¤t, sparking rate, number of fields on line weekly .Continuous opacity monitoring.An audible or visual alarm indicating ESP trouble.Inspections of rapper ops, TR set Ops, the ash removal system in the O&M plan.Major outage, check correct plate electrode alignment, inspect the collection surface for fouling, the mechanical condition of the TR set and inspect the interanal structural components. Corrective action procedures need to planned and ready to im plem ent upon exceedance or excursion. Maintain a record of the initial stack testing and subsequent testing.Maintain records of monitoring or control equipment malfunctions.Maintain corrective action records.Maintain records of annual Method 9 and any others.Maintain quarterly records of all 6-minute averages and monitor down time.Maintain a copy of all inspections and actions taken.Maintain records of maintenance and inspections.Maintain a spare parts inventory .Keep records available onsite for 5 y rs. Report no later than 10 days after any exceedance. 8 pound per million British Thermal Unit (lb/MMBtu)

No Permit limit The permitee shall install calibrate, maintain and operat a continuous emission monitor.Conduct daily calibration checks.Conduct RATA per Part 75. Maintain record of sulfur content of the fuel.Record the dily monioring system calibration check .Maintain records of fuel ty pe, verifying a sulfur content less than 0.5% for fuel oil.Determine heating value of fuel oil.Keep records available onsite for 5 yrs. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. 40 percent by

weight No Permit limit; percent, not percent-by-weight Continuous opacity

monitor required, with results to DAS.Calibrate, maintain and operate the COMs, conducting daily calibration check. Record daily

calibration.Record highest 6-minute average daily .Maintain records from COMs.Maintain records of opacity or monitoring equipment malfunctions.Maintain records of Method 9 visual observations.Keep records available onsite for 5 yrs. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. 0.055 pound per million British Thermal Unit (lb/MMBtu)

No Maintain ESP per O&M plan. Maintain record of initial and subsequent stack tests.Monitor for ESP performance, primary & secondary

voltage & current, sparking rate, and number of fields on line weekly .Take corrective action during excursions and document.An audible or visual alarm will indicate ESP trouble.Inspect rapper operation, TR set ops, and the maintenance plan, taking corrective actions as needed.During outages, check the correct plate electrode alignment, the inspection of the collection surface for fouling, the mechanical condition of the TR sets and the internal structural components.Maintain COMs, calibrate daily .Conduct RATA per Part 75. Maintain a record of the initial stack testing and any other subsequent testing or the test information for particulate matter.Maintain records of any monitoring or control equipment malfuncrions and corrective actions.Maintain records of any method 9 visual obervations.Opacity reports and supporting data shall be maintained. Maintain inspections and accompany ing actions.Record the daily calibrations.Record the highest 6-minute average opacity daily .Record all opacity exceedances and monitor down time.Keep records available onsite for 5 yrs. Report no later than 10 days after any exceedance. 11.5 percent by

weight No percent (not percent by weight Maintain continuous emissions monitoring equipment.Calibrate monitor daily .Measure O2 or CO2.Conduct RATA per Part 75

Opacity reports and supporting data shall be maintained. Maintain all inspections and actions taken.Record daily calibration and the highest 6-minute average per day .Maintain records of any opacity or monitoring equipment malfunctions.Maintain records of Method 9 visual observations.Keep records available onsite for 5 yrs. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time, with explanations.Certify operation of the COMs system. 1.2 pound per million British Thermal Unit (lb/MMBtu)

No Permit Limit - No scrubber. Limit is 0.80 lb/MMBTU for fuel oil Maintain continuous emissions monitoring equipment.Conduct a daily calibration.Conduct a RATA per Part 75. Maintain a record of CEM data including 3-hr rolling average data.Keep record of daily calibration.Keep records available onsite for 5 yrs. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time, with explanations.Certify operation of the CEMs system. 0.05 pound per million British Thermal Unit (lb/MMBtu)

No Maintain continuous emission monitoring equipment.Conduct a daily calibration.Conduct a RATA per Part 75. Maintain a record of CEM data including 3-hr rolling average data.Record daily calibrationsKeep records available onsite for 5 y rs. Report no later than 10 days after any exceedance.Report quaterly exceedances and monitor down time, with explanations.Certify operation of CEMs system.

Page 30configuration_pollutants1

Report no later than 10 days after any exceedance Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. Report no later than 10 days after any exceedance. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time. Report no later than 10 days after any exceedance. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time, with explanations.Certify operation of the COMs system. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time, with explanations.Certify operation of the CEMs system. Report no later than 10 days after any exceedance.Report quaterly exceedances and monitor down time, with explanations.Certify operation of CEMs system.

Page 31configuration_pollutants1

Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time, with explanations.Certify operation of the COMs system. Report no later than 10 days after any exceedance.Report quarterly exceedances and monitor down time, with explanations.Certify operation of the CEMs system. Report no later than 10 days after any exceedance.Report quaterly exceedances and monitor down time, with explanations.Certify operation of CEMs system.

Page 32control_technologies

facility _id configuration_id

component_id

control_id project_title project_ty pe vendor_name

vndor_contact

vendor_phone 2168 MB1 MB1 1 cyclean Non-Demonstration Clean Coal Solutiona

Nina French

3037340330 2168 MB2 MB2 2 Cyclean Non-Demonstration Clean Coal Solutions

Nina French

3037340330

Page 33control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive 8100 SouthPark W ay , Unit B

Littleton CO 80120 6/1/2010 8100 SouthPark W ay , Unit B

Littleton CO 80120 6/1/2010

Page 34control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units 40 1.8 lb/TBtu 40 2 lb/TBtu

Page 35control_technologies

feed_rate_units

Page 36control_coal_ranks

facility _id configuration_id

component_id

control_id coal_ty pe 2168 MB1 MB1 1 subbituminous 2168 MB2 MB2 2 subbituminous

Page 37control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e 2168 MB1 MB1 1 Total Mercury (Hgt) 2168 MB2 MB2 2 Total Mercury (Hgt)

Page 38control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year 2168 MB1 MB1 1 Yes No 0 0 2009 2168 MB2 MB2 2 Yes No 0 0 2009

Page 39control_costs

CBI FALSE FALSE

Page 40mi sc_controls

facility _id mi sc_control_id

control_description

Page 41mi sc_control_configurations

facility _id mi sc_control_id

configuration_id

Page 42fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 2168 April 4/1/2009 251295 short tons (2000 lbs) coal WY WY - Campbell 2168 August 8/1/2009 476161 short tons (2000 lbs) coal WY WY - Campbell 2168 December 12/1/2009 300723 short tons (2000 lbs) coal WY WY - Campbell 2168 Feb O 2/1/2009 oil MO MO - Chariton 2168 February 2/1/2009 448014 short tons (2000 lbs) coal WY WY - Campbell 2168 Jan Oil 1/1/2009 oil MO MO - Chariton 2168 January 1/1/2009 411048 short tons (2000 lbs) coal WY WY - Campbell 2168 July 7/1/2009 362883 short tons (2000 lbs) coal WY WY - Campbell 2168 June 6/1/2009 342140 short tons (2000 lbs) coal WY WY - Campbell 2168 June O 6/1/2009 oil MO MO - Chariton 2168 March 3/1/2009 338720 short tons (2000 lbs) coal WY WY - Campbell 2168 May 5/1/2009 407928 short tons (2000 lbs) coal WY WY - Campbell 2168 NARM Annual

12/1/2009 coal WY WY - Campbell 2168 Nov O 11/1/2009 oil MO MO - Chariton 2168 Novem ber 11/1/2009 379575 short tons (2000 lbs) coal WY WY - Campbell 2168 Oct O 10/1/2009 oil MO MO - Chariton 2168 October 10/1/2009 377116 short tons (2000 lbs) coal WY WY - Campbell 2168 Sept O 9/1/2009 oil MO MO - Chariton 2168 Septem ber 9/1/2009 348879 short tons (2000 lbs) coal WY WY - Campbell

Page 43fuel_shipments

coal_seam shipment_method Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train MO - Chariton Trucks

Wyodak-Anderson

Unit Train MO - Chariton Trucks

Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train MO - Chariton Trucks

Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train MO - Chariton Trucks

Wyodak-Anderson

Unit Train MO - Chariton Trucks

Wyodak-Anderson

Unit Train MO - Chariton Trucks

Wyodak-Anderson

Unit Train

Page 44fuel_shipment_configurations

facility _id shipment_id

configuration_id 2168 April MB1 2168 April MB2 2168 April MB3 2168 August MB1 2168 August MB2 2168 August MB3 2168 December MB1 2168 December MB2 2168 December MB3 2168 Feb O MB1 2168 Feb O MB2 2168 Feb O MB3 2168 February MB1 2168 February MB2 2168 February MB3 2168 Jan Oil MB1 2168 Jan Oil MB2 2168 Jan Oil MB3 2168 January MB1 2168 January MB2 2168 January MB3 2168 July MB1 2168 July MB2 2168 July MB3 2168 June MB1 2168 June MB2 2168 June MB3 2168 June O MB1 2168 June O MB2 2168 June O MB3 2168 March MB1 2168 March MB2 2168 March MB3 2168 May MB1 2168 May MB2 2168 May MB3 2168 NARM Annual

MB1 2168 NARM Annual

MB2 2168 NARM Annual

MB3 2168 Nov O MB1 2168 Nov O MB2 2168 Nov O MB3 2168 Novem ber MB1 2168 Novem ber MB2 2168 Novem ber MB3 2168 Oct O MB1 2168 Oct O MB2 2168 Oct O MB3 2168 October MB1 2168 October MB2 2168 October MB3

Page 45fuel_shipment_configurations

2168 Sept O MB1 2168 Sept O MB2 2168 Sept O MB3 2168 Septem ber MB1 2168 Septem ber MB2 2168 Septem ber MB3

Page 46fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 2168 April April 251295 tons 0.21 4.38 8729 Btu/lb 2168 August August 476161 tons 0.2 4.46 8627 Btu/lb 2168 December December 300723 tons 0.2 4.57 8746 Btu/lb 2168 Feb O February 113529 gallons 0.007 0.009 138020 Btu/gal 2168 February February 448014 tons 0.23 4.44 8667 Btu/lb 2168 Jan Oil January 112742 gallons 0.006 0.007 136765 Btu/gal 2168 January January 167827 tons 0.29 4.34 8768 Btu/lb 2168 July July 362883 tons 0.21 4.45 8662 Btu/lb 2168 June June 342140 tons 0.21 4.61 8650 Btu/lb 2168 June O July

2009 74228 gallons 0.004 0.002 128492 Btu/gal 2168 March March 338720 tons 0.21 4.38 8729 Btu/lb 2168 May May 407928 tons 0.29 4.69 8666 Btu/lb 2168 NARM Annual

2008 3043161 tons 2168 NARM Annual

2009 3135161 tons 2168 Nov O Novem ber 103390 gallons 0.005 0.003 137529 Btu/gal 2168 Novem ber Novem ber 379575 tons 0.21 4.48 8757 Btu/lb 2168 Oct O Oct 49334 gallons 0.008 0.007 137373 Btu/gal 2168 October October 377116 tons 0.2 4.36 8244 Btu/lb 2168 Sept O Septem ber 103729 gallons 0.004 0.002 137149 Btu/gal 2168 Septem ber Septem ber 348879 tons 0.19 4.53 8469 Btu/lb

Page 47fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_ty pe

supplier_name

supplier_address standard operational procedures Fuel supplier standard operational procedures Fuel supplier standard operational procedures Fuel supplier standard operational procedures Other standard operational procedures Fuel supplier standard operational procedures Other standard operational procedures Fuel supplier standard operational procedures Fuel supplier standard operational procedures Fuel supplier standard operational procedures Other standard operational procedures Fuel supplier standard operational procedures Fuel supplier 12.8 parts per million (dry) (ppm) 66 parts per million (dry) (ppm)

permit requirements Fuel supplier 10 parts per million (dry) (ppm) 75 parts per million (dry) (ppm)

permit requirements Fuel supplier standard operational procedures Other standard operational procedures Fuel supplier standard operational procedures Other standard operational procedures Fuel supplier standard operational procedures Other standard operational procedures Fuel supplier

Page 48fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies No No No No No No No No No No No No No No No No No No No No

Page 49fuel_shipment_samples

analysis_copies

Page 50fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 2168 NARM Annual

2008 Antim ony

(Sb) 1 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Arsenic (As) 1 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Barium (Ba) 350.3 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Beryllium (Be) 0.225 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Cadmium (Cd) 0.2 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Chromium (Cr) 3.67 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Cobalt (Co) 1.85 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Copper (Cu) 11.13 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Lead (Pb) 2.17 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Manganese (Mn) 7.35 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Mercury

(Hg) 0.061 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Molybdenum (Mo) 2.04 parts per million (dry) (ppm)

FALSE 2168 NARM Annual

2008 Nickel (Ni) 3.13 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Selenium (Se) 1 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2008 Vanadium (V) 10.27 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Antim ony

(Sb) 0.5 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Arsenic (As) 0.5 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Barium (Ba) 357 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Beryllium (Be) 0.2 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Cadmium (Cd) 0.1 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Chromium (Cr) 4 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Cobalt (Co) 2 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Copper (Cu) 11 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Lead (Pb) 1 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Manganese (Mn) 7 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Mercury

(Hg) 0.07 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Molybdenum (Mo) 1 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Nickel (Ni) 0.5 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Selenium (Se) 0.5 parts per million (dry) (ppm) FALSE 2168 NARM Annual

2009 Vanadium (V) 11 parts per million (dry) (ppm) FALSE

Page 51test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 2168 Catalyst Mercury Test other Information for Compliance Planning Stack Mercury , Ontario Hydro Test

9/7/2005 9/7/2005 No No 2168 Catalyst Mercury Test U2 other Information for Compliance Planning Stack Mercury , Ontario Hydro Test

9/7/2005 9/7/2005 No No 2168 Catalyst Mercury Test U3 other Information for Compliance Planning Stack Mercury , Ontario Hydro Test

9/8/2005 9/8/2005 No No 2168 ESP Performance Testing

other ESP Outlet Em ission Rate Unit 3 ESP Performance Testing Report for Thomas Hill

6/27/2008 6/27/2008 No No

Page 52test_reports

deviation_reports No No No No

Page 53test_report_configurations

facility _id report_id configuration_id 2168 Catalyst Mercury Test MB1 2168 Catalyst Mercury Test U2 MB2 2168 Catalyst Mercury Test U3 MB3 2168 ESP Performance Testing

MB3

Page 54test_report_fuels

facility _id report_id fuel_id 2168 Catalyst Mercury Test coal 2168 Catalyst Mercury Test U2 Coal 2168 Catalyst Mercury Test U3 coal 2168 ESP Performance Testing

coal

Page 55test_report_fuel_ty pes

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 2168 Catalyst Mercury Test coal coal - subbituminous 100 100 2168 Catalyst Mercury Test U2 Coal coal - subbituminous 100 100 2168 Catalyst Mercury Test U3 coal coal - subbituminous 100 100 2168 ESP Performance Testing

coal coal - subbituminous 100 100

Page 56cem_data

facility _id tim e_period

cem_period_description

Page 57cem_data_pollutants1

facility _id tim e_period

pollutant_nam e

Page 58test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_by pass_percent

testing_by pass_percent 2168 Catalyst Mercury Test 8-1 No No 2168 Catalyst Mercury Test U2 8-2 No No 2168 Catalyst Mercury Test U3 8-3 No No 2168 ESP Performance Testing

7-3 No No

Page 59test_report_sampling

fg_fraction 100% 100 100% ESP Outlet Ducts A&B - 100% of flow from Unit 3 boiler

Page 60sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 2168 Catalyst Mercury Test 8-1 1 9/7/2005 9/7/2005 197 12.5 2168 Catalyst Mercury Test 8-1 2 9/7/2005 9/7/2005 192 11.6 2168 Catalyst Mercury Test 8-1 3 9/7/2005 9/7/2005 192 12.6 2168 Catalyst Mercury Test U2 8-2 1 9/7/2005 9/7/2005 197 12 2168 Catalyst Mercury Test U2 8-2 2 9/7/2005 9/7/2005 192 11.4 2168 Catalyst Mercury Test U2 8-2 3 9/7/2005 9/7/2005 192 11.4 2168 Catalyst Mercury Test U3 8-3 1 9/8/2005 9/8/2005 197 10.3 2168 Catalyst Mercury Test U3 8-3 2 9/8/2005 9/8/2005 192 10 2168 Catalyst Mercury Test U3 8-3 3 9/8/2005 9/8/2005 192 10.3 2168 ESP Performance Testing

7-3 1 6/27/2008 6/27/2008 712 670 13.82 2168 ESP Performance Testing

7-3 2 6/27/2008 6/27/2008 705 660 14.36 2168 ESP Performance Testing

7-3 3 6/27/2008 6/27/2008 707 665 13.45

Page 61sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 416059 dscfm 94 29.4 4.1 15 300 416491 dscfm 94 29.4 4.1 15 300 411222 dscfm 92 29.4 4.1 15 300 557413 dscfm 92 29.5 4.1 14.9 300 562608 dscfm 96 29.5 4.1 14.9 300 565430 dscfm 95 29.5 4.1 14.9 300 534064 dscfm 88 29.45 5 14.4 300 536636 dscfm 93 29.45 4.9 14.5 300 534271 dscfm 92 29.45 4.9 14.6 300 1581904 dscfm 29.85 7 15.8 282 1713241 dscfm 29.85 7 16 287 1752185 dscfm 29.85 7 16 290

Page 62sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 29.37 Ontario Hydro Normal flue gas temperatures are > 300, although software allows max entry of 300 degrees. Stack temp was 347 degrees. coal 197 29.37 Ontario Hydro Normal flue gas temperatures are > 300, although software allows max entry of 300 degrees. Stack temp was 348 degrees. 29.37 Ontario Hydro Normal flue gas temperatures are > 300, although software allows max entry of 300 degrees. Stack temp was 347 degrees. 29.45 Ontario Hydro Actual stack temp was 347 degrees, which is normal for this unit. 29.45 Ontario Hydro Actual stack temp was 351 degrees, which is normal for this unit. 29.45 Ontario Hydro Actual stack temp was 349 degrees, which is normal for this unit. 29.39 Ontario Hydro Actual stack gas temperature was 327 degrees, which is normal for this unit.

coal 29.39 Ontario Hydro Actual stack gas temperature was 331 degrees, which is normal for this unit. 29.39 Ontario Hydro Actual stack gas temperature was 332 degrees, which is normal for this unit. 28.63 me thod 17 28.63 Method 17 28.63 Method 17

Page 63sampling_runs

fuel_sulfur

Normal flue gas temperatures are > 300, although software allows max entry of 300 degrees. Stack temp was 348 degrees. Normal flue gas temperatures are > 300, although software allows max entry of 300 degrees. Stack temp was 347 degrees.

Actual stack gas temperature was 331 degrees, which is normal for this unit. Actual stack gas temperature was 332 degrees, which is normal for this unit.

Page 64sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 2168 Catalyst Mercury Test 8-1 1 Oxidized Mercury (Hg++) 1.23 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 1 Particulate-bound Mercury (Hgp) 0.02 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 1 Elem ental Mercury (Hg0) 0.12 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 1 Total Mercury (Hgt) 3.08 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 2 Particulate-bound Mercury (Hgp) 0.02 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 2 Oxidized Mercury (Hg++) 1.6 mi crogram per dry

standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 2 Elem ental Mercury (Hg0) 0.12 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 2 Total Mercury (Hgt) 3.69 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 3 Particulate-bound Mercury (Hgp) 0.02 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 3 Oxidized Mercury (Hg++) 1.4 mi crogram per dry

standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 3 Elem ental Mercury (Hg0) 1.73 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test 8-1 3 Total Mercury (Hgt) 3.14 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 1 Particulate-bound Mercury (Hgp) 0.05 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 1 Oxidized Mercury (Hg++) 0.85 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 1 Elem ental Mercury (Hg0) 2.76 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 1 Total Mercury (Hgt) 3.66 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 2 Particulate-bound Mercury (Hgp) 0.04 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 2 Oxidized Mercury (Hg++) 0.82 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 2 Elem ental Mercury (Hg0) 2.68 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 2 Total Mercury (Hgt) 3.54 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 3 Particulate-bound Mercury (Hgp) 0.03 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 3 Oxidized Mercury (Hg++) 0.34 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 3 Elem ental Mercury (Hg0) 3.12 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U2 8-2 3 Total Mercury (Hgt) 3.49 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 1 Particulate-bound Mercury (Hgp) 0.02 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 1 Oxidized Mercury (Hg++) 0.75 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 1 Elem ental Mercury (Hg0) 4.32 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 1 Total Mercury (Hgt) 5.09 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 2 Particulate-bound Mercury (Hgp) 0.004 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 2 Oxidized Mercury (Hg++) 0.75 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 2 Elem ental Mercury (Hg0) 4.27 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 2 Total Mercury (Hgt) 5.03 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 3 Particulate-bound Mercury (Hgp) 0.01 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 3 Oxidized Mercury (Hg++) 0.88 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 3 Elem ental Mercury (Hg0) 4.52 mi crogram per dry standard cubic meter ( FALSE 2168 Catalyst Mercury Test U3 8-3 3 Total Mercury (Hgt) 5.41 mi crogram per dry standard cubic meter ( FALSE 2168 ESP Performance Testing

7-3 1 PM (Filterable) FALSE 2168 ESP Performance Testing

7-3 2 PM (Filterable) FALSE 2168 ESP Performance Testing

7-3 3 PM (Filterable) FALSE

Page 65sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 0.00192 pound per hour (lb/hr)

FALSE 0.94 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 3.69E-05 pound per hour (lb/hr) FALSE 0.02 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00284 pound per hour (lb/hr)

FALSE 1.39 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0048 pound per hour (lb/hr)

FALSE 2.34 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 3.79E-05 pound per hour (lb/hr) FALSE 0.02 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0025 pound per hour (lb/hr)

FALSE 1.22 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00322 pound per hour (lb/hr)

FALSE 1.57 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00576 pound per hour (lb/hr)

FALSE 2.8 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 2.96E-05 pound per hour (lb/hr) FALSE 0.01 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00215 pound per hour (lb/hr)

FALSE 1.06 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00266 pound per hour (lb/hr)

FALSE 1.31 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00484 pound per hour (lb/hr)

FALSE 2.39 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000108 pound per hour (lb/hr) FALSE 0.04 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00178 pound per hour (lb/hr)

FALSE 0.65 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00575 pound per hour (lb/hr)

FALSE 2.09 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00764 pound per hour (lb/hr)

FALSE 2.78 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 9.46E-05 pound per hour (lb/hr) FALSE 0.03 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00174 pound per hour (lb/hr)

FALSE 0.63 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00564 pound per hour (lb/hr)

FALSE 2.04 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00747 pound per hour (lb/hr)

FALSE 2.71 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 7.29E-05 pound per hour (lb/hr) FALSE 0.03 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000729 pound per hour (lb/hr) FALSE 0.26 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0066 pound per hour (lb/hr)

FALSE 2.37 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0074 pound per hour (lb/hr)

FALSE 2.65 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 4.49E-05 pound per hour (lb/hr) FALSE 0.02 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0015 pound per hour (lb/hr)

FALSE 0.6 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00864 pound per hour (lb/hr)

FALSE 3.46 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0102 pound per hour (lb/hr)

FALSE 4.08 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 7.57E-06 pound per hour (lb/hr) FALSE 0.003 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00151 pound per hour (lb/hr)

FALSE 0.6 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00859 pound per hour (lb/hr)

FALSE 3.41 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0101 pound per hour (lb/hr)

FALSE 4.01 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 1.54E-05 pound per hour (lb/hr) FALSE 0.01 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00177 pound per hour (lb/hr)

FALSE 0.71 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.00904 pound per hour (lb/hr)

FALSE 3.6 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.0108 pound per hour (lb/hr)

FALSE 4.32 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 33.8 pound per hour (lb/hr)

FALSE FALSE 43.08 pound per hour (lb/hr)

FALSE FALSE 39.76 pound per hour (lb/hr)

FALSE FALSE

Page 66sampling_run_pollutants1

run_pollutant_comment

Page 67sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL 2168 Catalyst Mercury Test 8-1 1 Mercury (Hg) FALSE

Page 68sampling_run_fuel

fuel_conc_MDL

Page 69