Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, January 14, 2011 Page 1 of 18
Facility Information:

AES Puerto Rico

CARRETERA #3 KM 142

GUAYAMA PR 00784

Contact: William G. Vela

Phone: 787-866-8117

Fax:

Email:

Testing Company:

URS Corporation

1600 Perimeter Park Drive, Suite 400

Morrisville NC 27560

Contact:Brad Justus

Phone: 919-461-1326

Fax: 919-461-1415

Email: brad_justus@urscorp.com

Air Permit Number:

68029

Permitted Source ID/Name:

Unit 2

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

*******

Industry/SCC/NAIS 221122

Sampling Location Information:

Test Parameter Information:

AFS #: 7205700056 FRS #:

SCC / Description 10100218 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Atmospheric Fluidized Bed Combustion: Circulating Bed (Bitum. Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 192 0 0 0 2304 2688 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Friday, January 14, 2011 Page 2 of 18
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Cobalt Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Friday, January 14, 2011 Page 3 of 18
Sampling / Stack Data Results Summary

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 3/14/2010 3/15/2010 3/15/2010

Run Start Time 2:15:00 PM 8:23:00 

AM

12:33:00 PM

Run Finish Time 5:36:00 PM 11:42:00 

AM

3:53:00 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 87.374 103.526 109.503 100.134

Moisture Content of Stack Gas, % 13.89 13.68 0.00 9.190

Moisture Saturation at Stack Gas Temperature, % 50.68 50.90 49.23 50.270

Carbon Dioxide, % 13.2 13.2 13.2 13.200

Oxygen, % 5.6 5.7 6 5.767

Average Stack Gas Temperature, °F 179.50 179.42 177.92 178.947

Dry Volumetric Flow Rate, dry scfm 592,448.7 593,014.9 668,262.2 617,908.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 837,222.2 840,961.9 816,110.7 831,431.600

Percent Isokinetic of Sampling Rate, % 103.3 97.0 91.0 97.100

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 4 of 18
Location Stack Exit - Method 29 

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Friday, January 14, 2011 Page 5 of 18
Emissions Summary

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 1.15E-03 3.95E-04 0.001

ppm 0.00E+00 7.28E-01 2.57E-01 0.328

ppm@7%O2 0.00E+00 6.84E-01 2.35E-01 0.306

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.297 0.323 0.345 0.322

Elb/hr 2.66E-01 2.45E-01 2.79E-01 0.263

lb/mmBtuO2 1.00E-04 9.25E-05 9.53E-05 0.000

mg/dscm 1.20E-01 1.10E-01 1.11E-01 0.114

mg/dscm@7%O2 1.09E-01 1.01E-01 1.04E-01 0.105

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.305 0.331 0.354 0.330

Elb/hr 2.74E-01 2.51E-01 2.86E-01 0.270

lb/mmBtuO2 1.03E-04 9.48E-05 9.78E-05 0.000

mg/dscm 1.23E-01 1.13E-01 1.14E-01 0.117

mg/dscm@7%O2 1.12E-01 1.03E-01 1.06E-01 0.107

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00221 0.00171 0.00121 0.002

Elb/hr 1.22E-03 9.47E-04 6.67E-04 0.001

lb/mmBtuO2 4.83E-07 3.72E-07 2.59E-07 0.000

mg/dscm 5.53E-04 4.32E-04 3.04E-04 0.000

mg/dscm@7%O2 5.26E-04 4.06E-04 2.82E-04 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00619 0.00488 0.00318 0.005

Elb/hr 3.41E-03 2.70E-03 1.75E-03 0.003

lb/mmBtuO2 1.35E-06 1.06E-06 6.80E-07 0.000

mg/dscm 1.55E-03 1.23E-03 7.99E-04 0.001

mg/dscm@7%O2 1.48E-03 1.16E-03 7.40E-04 0.001

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00059 0.00042 0.00034 0.000

Friday, January 14, 2011 Page 6 of 18
Elb/hr 3.25E-04 2.33E-04 1.88E-04 0.000

lb/mmBtuO2 1.29E-07 9.14E-08 7.27E-08 0.000

mg/dscm 1.48E-04 1.06E-04 8.54E-05 0.000

mg/dscm@7%O2 1.41E-04 9.96E-05 7.91E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00062 0.00034 0.00025 0.000

Elb/hr 3.42E-04 1.88E-04 1.38E-04 0.000

lb/mmBtuO2 1.35E-07 7.40E-08 5.34E-08 0.000

mg/dscm 1.55E-04 8.58E-05 6.28E-05 0.000

mg/dscm@7%O2 1.48E-04 8.06E-05 5.82E-05 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.01243 0.00931 0.00671 0.009

Elb/hr 6.85E-03 5.16E-03 3.70E-03 0.005

lb/mmBtuO2 2.72E-06 2.03E-06 1.43E-06 0.000

mg/dscm 3.11E-03 2.35E-03 1.69E-03 0.002

mg/dscm@7%O2 2.96E-03 2.21E-03 1.57E-03 0.002

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00891 0.00609 0.00423 0.006

Elb/hr 4.91E-03 3.37E-03 2.33E-03 0.004

lb/mmBtuO2 1.95E-06 1.33E-06 9.04E-07 0.000

mg/dscm 2.23E-03 1.54E-03 1.06E-03 0.002

mg/dscm@7%O2 2.12E-03 1.45E-03 9.82E-04 0.002

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 244.5 194.7 123.8 187.667

Elb/hr 1.35E+02 1.08E+02 6.83E+01 103.767

lb/mmBtuO2 5.34E-02 4.24E-02 2.65E-02 0.041

mg/dscm 6.11E+01 4.92E+01 3.11E+01 47.133

mg/dscm@7%O2 5.82E+01 4.62E+01 2.88E+01 44.400

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00637 0.00408 0.00417 0.005

Elb/hr 3.51E-03 2.26E-03 2.30E-03 0.003

lb/mmBtuO2 1.39E-06 8.88E-07 8.91E-07 0.000

mg/dscm 1.59E-03 1.03E-03 1.05E-03 0.001

mg/dscm@7%O2 1.51E-03 9.67E-04 9.73E-04 0.001

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.02545 0.01586 0.01086 0.017

Friday, January 14, 2011 Page 7 of 18
Elb/hr 1.40E-02 8.79E-03 5.99E-03 0.010

lb/mmBtuO2 5.56E-06 3.45E-06 2.32E-06 0.000

mg/dscm 6.36E-03 4.00E-03 2.73E-03 0.004

mg/dscm@7%O2 6.06E-03 3.76E-03 2.53E-03 0.004

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.03333 0.01953 0.00733 0.020

Elb/hr 1.84E-02 1.08E-02 4.04E-03 0.011

lb/mmBtuO2 7.28E-06 4.25E-06 1.57E-06 0.000

mg/dscm 8.33E-03 4.93E-03 1.84E-03 0.005

mg/dscm@7%O2 7.93E-03 4.63E-03 1.71E-03 0.005

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0063 0.0039 0.00287 0.004

Elb/hr 3.47E-03 2.16E-03 1.58E-03 0.002

lb/mmBtuO2 1.38E-06 8.49E-07 6.13E-07 0.000

mg/dscm 1.58E-03 9.85E-04 7.21E-04 0.001

mg/dscm@7%O2 1.50E-03 9.25E-04 6.68E-04 0.001

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 118 85.2 86.2 96.467

lb/mmBtuO2 3.15E-02 2.22E-02 2.21E-02 0.025

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 13.3 11.9 0.0143 8.405

lb/mmBtuO2 3.55E-03 3.10E-03 3.66E-06 0.002

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 252.3 357.3 172 260.533

lb/mmBtuO2 6.74E-02 9.31E-02 4.40E-02 0.068

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 3.5 2.6 1.9 2.667

lb/mmBtuO2 9.34E-04 6.77E-04 4.86E-04 0.001

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 373.8 445.1 260.1 359.667

lb/mmBtuO2 9.98E-02 1.16E-01 6.66E-02 0.094

Friday, January 14, 2011 Page 8 of 18
Process Run Data

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 269.1 371.8 188.2 276.367

lb/mmBtuO2 7.18E-02 9.69E-02 4.82E-02 0.072

Friday, January 14, 2011 Page 9 of 18
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 0 Tons 0

1 Average Heat Input 2284.5 MMBtu/hr 0

1 Steam Output 1000 lb steam/hr 0

1 Fuel Oil Firing Rate 0 0

1 Standard Pressure 0 atm 0

1 Standard Temperature 180 Deg F 0

1 Unit Gross Electrical Output 254 MW 0

1 Unit Net Electric Generation 0 MWh 0

2 Bituminous Coal Burned 0 Tons 0

2 Average Heat Input 2284.5 MMBtu/hr 0

2 Steam Output 0 1000 lb steam/hr 0

2 Fuel Oil Firing Rate 0 0

2 Standard Pressure 0 atm 0

2 Standard Temperature 180 Deg F 0

2 Unit Gross Electrical Output 254 MW 0

2 Unit Net Electric Generation 0 MWh 0

3 Bituminous Coal Burned 0 Tons 0

3 Average Heat Input 2284.5 MMBtu/hr 0

3 Steam Output 0 1000 lb steam/hr 0

3 Fuel Oil Firing Rate 0 0

3 Standard Pressure 0 atm 0

3 Standard Temperature 178 Deg F 0

3 Unit Gross Electrical Output 254 MW 0

3 Unit Net Electric Generation 0 MWh 0

4 Bituminous Coal Burned 0 Tons 0

4 Average Heat Input 2241.8 MMBtu/hr 0

4 Steam Output 0 1000 lb steam/hr 0

4 Fuel Oil Firing Rate 0 0

4 Standard Pressure 0 atm 0

4 Standard Temperature 178 Deg F 0

4 Unit Gross Electrical Output 255 MW 0

4 Unit Net Electric Generation 0 MWh 0

5 Bituminous Coal Burned 0 Tons 0

Friday, January 14, 2011 Page 10 of 18
5 Average Heat Input 2241.8 MMBtu/hr 0

5 Steam Output 0 1000 lb steam/hr 0

5 Fuel Oil Firing Rate 0 0

5 Standard Pressure 0 atm 0

5 Standard Temperature 178 Deg F 0

5 Unit Gross Electrical Output 255 MW 0

5 Unit Net Electric Generation 0 MWh 0

6 Bituminous Coal Burned 0 Tons 0

6 Average Heat Input 2263.1 MMBtu/hr 0

6 Steam Output 0 1000 lb steam/hr 0

6 Fuel Oil Firing Rate 0 0

6 Standard Pressure 0 atm 0

6 Standard Temperature 178 Deg F 0

6 Unit Gross Electrical Output 255 MW 0

6 Unit Net Electric Generation 0 MWh 0

7 Bituminous Coal Burned 0 Tons 0

7 Average Heat Input 2284.5 MMBtu/hr 0

7 Steam Output 0 1000 lb steam/hr 0

7 Fuel Oil Firing Rate 0 0

7 Standard Pressure 0 atm 0

7 Standard Temperature 178 Deg F 0

7 Unit Gross Electrical Output 255 MW 0

7 Unit Net Electric Generation 0 MWh 0

8 Bituminous Coal Burned 0 Tons 0

8 Average Heat Input 2284.5 MMBtu/hr 0

8 Steam Output 0 1000 lb steam/hr 0

8 Fuel Oil Firing Rate 0 0

8 Standard Pressure 0 atm 0

8 Standard Temperature 178 Deg F 0

8 Unit Gross Electrical Output 255 MW 0

8 Unit Net Electric Generation 0 MWh 0

9 Bituminous Coal Burned 0 Tons 0

9 Average Heat Input 2284.5 MMBtu/hr 0

9 Steam Output 0 1000 lb steam/hr 0

9 Fuel Oil Firing Rate 0 0

9 Standard Pressure 0 atm 0

Friday, January 14, 2011 Page 11 of 18
APCD Run Data

Process Lab Run Data

9 Standard Temperature 178 Deg F 0

9 Unit Gross Electrical Output 255 MW 0

9 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 10757 Btu/lb

2 Fuel Higher Heating Value 10825 Btu/lb

3 Fuel Higher Heating Value 10733 Btu/lb

4 Fuel Higher Heating Value 11281 Btu/lb

5 Fuel Higher Heating Value 10973 Btu/lb

6 Fuel Higher Heating Value Btu/lb

7 Fuel Higher Heating Value 11021 Btu/lb

8 Fuel Higher Heating Value 10630 Btu/lb

9 Fuel Higher Heating Value 10158 Btu/lb

1 Fuel Moisture 13 %

2 Fuel Moisture 12 %

3 Fuel Moisture 13 %

4 Fuel Moisture 11.5 %

5 Fuel Moisture 13.1 %

6 Fuel Moisture %

7 Fuel Moisture 12 %

8 Fuel Moisture 12 %

9 Fuel Moisture 11 %

1 Fuel Mercury Content 0.117 ppm

2 Fuel Mercury Content 0.095 ppm

3 Fuel Mercury Content 0.097 ppm

4 Fuel Mercury Content 0.074 ppm

5 Fuel Mercury Content 0.07 ppm

6 Fuel Mercury Content ppm

7 Fuel Mercury Content 0 ppm

8 Fuel Mercury Content 0 ppm

9 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0.5 ppm

2 Fuel Cadmium Content 0.66 ppm

3 Fuel Cadmium Content 0.63 ppm

4 Fuel Cadmium Content 0.5 ppm

5 Fuel Cadmium Content 0.51 ppm

6 Fuel Cadmium Content ppm

Friday, January 14, 2011 Page 12 of 18
7 Fuel Cadmium Content

0 ppm

8 Fuel Cadmium Content0 ppm

9 Fuel Cadmium Content0 ppm

1 Ultimate/Proximate Analysis0

2 Ultimate/Proximate Analysis0

3 Ultimate/Proximate Analysis0

4 Ultimate/Proximate Analysis0

5 Ultimate/Proximate Analysis0

6 Ultimate/Proximate Analysis 7 Ultimate/Proximate Analysis

0

8 Ultimate/Proximate Analysis0

9 Ultimate/Proximate Analysis0

1 Fuel Nickel Content 6.8 ppm 2 Fuel Nickel Content 9.6 ppm 3 Fuel Nickel Content 8.3 ppm 4 Fuel Nickel Content 12 ppm 5 Fuel Nickel Content 10 ppm 6 Fuel Nickel Content ppm 7 Fuel Nickel Content 0 ppm 8 Fuel Nickel Content 0 ppm 9 Fuel Nickel Content 0 ppm 1 Fuel Arsenic Content 5.6 ppm 2 Fuel Arsenic Content 16 ppm 3 Fuel Arsenic Content 7.2 ppm 4 Fuel Arsenic Content 8.9 ppm 5 Fuel Arsenic Content 8.5 ppm 6 Fuel Arsenic Content ppm 7 Fuel Arsenic Content 0 ppm 8 Fuel Arsenic Content 0 ppm 9 Fuel Arsenic Content 0 ppm 1 Fuel Chromium Content 5.4 ppm 2 Fuel Chromium Content 5.1 ppm 3 Fuel Chromium Content 4.9 ppm 4 Fuel Chromium Content 6.1 ppm 5 Fuel Chromium Content 5.7 ppm 6 Fuel Chromium Content ppm 7 Fuel Chromium Content 0 ppm 8 Fuel Chromium Content 0 ppm 9 Fuel Chromium Content 0 ppm 1 Fuel Beryllium Content 0.53 ppm 2 Fuel Beryllium Content 0.6 ppm 3 Fuel Beryllium Content 0.64 ppm 4 Fuel Beryllium Content 0.71 ppm

Friday, January 14, 2011 Page 13 of 18
5 Fuel Beryllium Content 0.58 ppm 6 Fuel Beryllium Content ppm 7 Fuel Beryllium Content 0 ppm 8 Fuel Beryllium Content 0 ppm 9 Fuel Beryllium Content 0 ppm 1 Fuel Lead Content 2.2 ppm 2 Fuel Lead Content 2.7 ppm 3 Fuel Lead Content 3 ppm 4 Fuel Lead Content 2.7 ppm 5 Fuel Lead Content 2.5 ppm 6 Fuel Lead Content ppm 7 Fuel Lead Content 0 ppm 8 Fuel Lead Content 0 ppm 9 Fuel Lead Content 0 ppm 1 Fuel Manganese Content 20 ppm 2 Fuel Manganese Content 64 ppm 3 Fuel Manganese Content 18 ppm 4 Fuel Manganese Content 32 ppm 5 Fuel Manganese Content 20 ppm 6 Fuel Manganese Content ppm 7 Fuel Manganese Content 0 ppm 8 Fuel Manganese Content 0 ppm 9 Fuel Manganese Content 0 ppm 1 Fuel Chlorine Content 56 ppm 2 Fuel Chlorine Content 60 ppm 3 Fuel Chlorine Content 63 ppm 4 Fuel Chlorine Content 50 ppm 5 Fuel Chlorine Content 50 ppm 6 Fuel Chlorine Content ppm 7 Fuel Chlorine Content 46 ppm 8 Fuel Chlorine Content 45 ppm 9 Fuel Chlorine Content 45 ppm 1 Fuel Fluorine Content 0 ppm 2 Fuel Fluorine Content 0 ppm 3 Fuel Fluorine Content 0 ppm 4 Fuel Fluorine Content 0 ppm 5 Fuel Fluorine Content 0 ppm 6 Fuel Fluorine Content ppm 7 Fuel Fluorine Content 29 ppm 8 Fuel Fluorine Content 32 ppm 9 Fuel Fluorine Content 33 ppm

Friday, January 14, 2011 Page 14 of 18
Sampling / Stack Data Results Detail

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, January 14, 2011 Page 15 of 18
Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 3/14/2010 3/15/2010 3/15/2010

Run Start Time 2:15:00 PM 8:23:00 AM 12:33:00 PM

Run Finish Time 5:36:00 PM 11:42:00 AM 3:53:00 PM

Net Traversing Points 36 36 36

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.171 0.192 0.192 0.185

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.005 1.005 1.005 1.005

Barometric Pressure, inches of Mercury 29.86 29.68 29.68 29.740

Average Orifice Meter Differential, inches H2O 0.83 1.27 1.27 1.123

Dry Gas Meter Volume Sampled, cubic feet 91.076 108.063 113.644 104.261

Average Dry Gas Meter Temperature, °F 93.14 91.18 88.01 90.777

Dry Gas Meter Volume Sampled, dscf 87.374 103.526 109.503 100.134

Total Moisture Liquid collected, g 299.3 348.7 0 216.000

Volume of Water Vapor, standard cubic feet 14.09 16.41 0.00 10.167

Moisture Content of Stack Gas, % 13.89 13.68 0.00 9.190

Moisture Saturation at Stack Gas Temperature, % 50.68 50.90 49.23 50.270

Dry Mole Fraction 0.8611 0.8632 1 0.908

Carbon Dioxide, % 13.2 13.2 13.2 13.200

Oxygen, % 5.6 5.7 6 5.767

Carbon Monoxide & Nitrogen, % 81.2 81.1 80.8 81.033

Fuel Factor 1.16 1.15 1.13

Dry Molecular Weight, lb/lb-Mole 30.34 30.34 30.35 30.343

Wet Molecular weight, lb/lb-Mole 28.63 28.65 30.35 29.210

Flue Gas Static Pressure, inches of H2O -1.1 -1.1 -1.1 -1.100

Absolute Flue Gas Pressure, inches of Mercury 29.78 29.60 29.60 29.660

Average Stack Gas Temperature, °F 179.50 179.42 177.92 178.947

Average Velocity Head, inches of H2O 1.2451191143

0368

1.249875885

13898

1.249875885

13898

1.248

Average Stack Gas Velocity, feet/second 69.40 69.71 67.65 68.920

Stack Cross-Sectional Area, square feet 201.062 201.062 201.062 201.062

Dry Volumetric Flow Rate, dry scfm 592,448.7 593,014.9 668,262.2 617,908.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 837,222.2 840,961.9 816,110.7 831,431.600

Percent Isokinetic of Sampling Rate, % 103.3 97.0 91.0 97.100

Percent Excess Air, % 35.4 36.3 39.1 36.933

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 192 192 192

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 16 of 18
Location Stack Exit - Method 29 

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, January 14, 2011 Page 17 of 18
Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, January 14, 2011 Page 18 of 18