NUREG/CR-6992 

Instrumentation and 

Controls in Nuclear Power 

Plants: An Emerging 

Technologies Update

Office of Nuclear Regulatory Research 
This Page Intentionally Left Blank
NUREG/CR-6992 

Instrumentation and 

Controls in Nuclear Power 

Plants: An Emerging 

Technologies Update 

Manuscript Completed: December 2008 

Date Published: October 2009 

Prepared by 

K. Korsaha, D.E. Holcomba, M.D. Muhlheima, 

J.A. Mullensa, A. Loebla, M. Bobreka, M.K. Howladera, 

S.M. Killougha, M.R. Moorea, P.D. Ewinga, M. Sharpeb, 

A.A. Shourbajia, S.M. Cetinera, T.L. Wilson, Jr.a, 

R.A. Kisnera 

a

Oak Ridge National Laboratory 

1 Bethel Valley Road 

Oak Ridge, TN 37831 

b

University of Tennessee 

315 Pasqua Engineering Building 

Knoxville, TN 37996-2300 

K. Nguyen and T. Govan, NRC Project Managers 

NRC Job Code Y6962 

Office of Nuclear Regulatory Research 
This Page Intentionally Left Blank
iii 

ABSTRACT 

This report is a summary of advances in eight instrumentation and controls (I&C) technology focus 

areas that have applications in nuclear power plant digital upgrades as well as in new plants. The 

review includes I&C architectures for selected Gen III+ plants. This report is the third in a series of 

planned update reports in a U.S. Nuclear Regulatory Commission (NRC) sponsored emerging 

technologies study. The first in the series was NUREG/CR-6812,TPD

1

DPT and the second was 

NUREG/CR-6888.TPD

2

DPT The study is designed to provide advance information that will enable NRC to be 

better prepared to make regulatory decisions in these areas. 

Compilation of this report generally follows the pattern established in the two previous series reports 

of reviewing advances in several technology focus areas. However, based on the results of the 

program review in FY 2006, in which the focus of the study was redirected to include digital I&C in 

new plants, the focus areas were slightly modified to include I&C architectures in new plants. Thus, 

the following are the focus areas used for this third NUREG/CR in the series: (1) sensors and 

measurement systems, (2) communications media and networking, (3) microprocessors and other 

integrated circuits, (4) computational platforms, (5) surveillance, diagnostics, and prognostics, (6) 

human-system interactions, (7) high-integrity software, and (8) I&C architectures in new plants. This 

report documents findings from the study of these focus areas. 
This Page Intentionally Left Blank
v 

FOREWORD 

This contractor-prepared NUREG-series report is the third in a series and provides an updated 

investigation of emerging instrumentation and controls (I&C) technologies and their applications in 

nuclear power plants (NPPs). The first in the series is NUREG/CR-6812, “Emerging Technologies in 

Instrumentation and Controls,” dated March 2003 and the second is NUREG/CR-6888, “Emerging 

Technologies in Instrumentation and Controls: An Update,” dated January 2006. This investigation 

was conducted by Oak Ridge National Laboratory, under contract to the U.S. Nuclear Regulatory 

Commission (NRC), using a similar research approach as used for the two previous NUREG/CRs to 

periodically provide the status of both current and emerging technologies that are likely to be used in 

NPPs. 

The primary objective of this report is to inform NRC staff of emerging I&C technologies and 

applications that are being studied or developed for use in both operating and new NPPs. The focus 

of this report is the review of eight technology areas: (1) sensors and measurement systems, 

(2) communications media and networking, (3) microprocessors and other integrated circuits, 

(4) computational platforms, (5) surveillance, diagnostics, and prognostics, (6) human-system 

interactions, (7) high-integrity software, and (8) I&C architectures in new plants. Several new reactor 

designs [e.g., the U.S. Evolutionary Pressurized Reactor (US-EPR) by AREVA NP and the Advanced 

Pressurized-Water Reactor (APWR) by Mitsubishi Heavy Industries] were chosen in reviewing the 

I&C technologies and applications. This report will provide the NRC staff updated information 

supporting regulatory work in I&C technology areas. 
This Page Intentionally Left Blank
vii 

CONTENTS 

Page 

TUABSTRACTUT .....................................................................................................................................iii

TUFOREWORDUT..................................................................................................................................... v

TUCONTENTSUT ....................................................................................................................................vii

TULIST OF FIGURESUT.......................................................................................................................... xi

TULIST OF TABLESUT .........................................................................................................................xiii

TUEXECUTIVE SUMMARYUT............................................................................................................. xv

TUABBREVIATIONS AND ACRONYMSUT....................................................................................... xxi

TU1. INTRODUCTIONUT........................................................................................................................ 1

TU1.1UT TUBACKGROUNDUT ............................................................................................................... 1

TU1.2UT TUSCOPE OF STUDYUT .......................................................................................................... 1

TU1.3UT TURESEARCH APPROACHUT ................................................................................................ 1

TU1.4UT TUSTRUCTURE OF REPORTUT.............................................................................................. 1

TU2. SENSORS AND MEASUREMENT SYSTEMSUT......................................................................... 3

TU2.1UT TUSENSORS AND MEASUREMENT SYSTEMS OVERVIEWUT........................................ 3

TU2.2UT TUDETAILS OF SELECTED SENSORSUT ............................................................................. 3

TU2.2.1UT TUDistributed Fiber-Optic Bragg ThermometryUT ..................................................... 4

TU2.2.2UT TUUltrasonic Wireline ThermometryUT ...................................................................... 5

TU2.2.3UT TUJohnson Noise ThermometryUT .............................................................................. 5

TU2.2.4UT TUGamma ThermometersUT........................................................................................ 7

TU2.2.5UT TUType-N ThermocouplesUT ...................................................................................... 7

TU2.3UT TUREGULATORY IMPACT OF SENSORS AND MEASUREMENT SYSTEM 

TECHNOLOGIESUT............................................................................................................. 8

TU3. COMMUNICATION MEDIA AND NETWORKINGUT ............................................................. 11

TU3.1UT TUCOMMUNICATION MEDIA AND NETWORKING OVERVIEWUT............................. 11

TU3.2UT TUDETAILS OF TECHNOLOGY/INDUSTRY TRENDSUT................................................. 11

TU3.2.1UT TUWired Instrument NetworksUT.............................................................................. 11

TU3.2.2UT TUWireless CommunicationsUT ................................................................................ 15

TU3.3UT TUREGULATORY IMPACT OF COMMUNICATIONS AND NETWORKINGUT .............. 21

TU4. MICROPROCESSORS AND OTHER INTEGRATED CIRCUITSUT......................................... 23

TU4.1UT TUMICROPROCESSORS AND OTHER INTEGRATED CIRCUITS OVERVIEWUT........ 23

TU4.2UT TUTECHNOLOGY TRENDSUT.............................................................................................. 23

TU4.2.1UT TUJosephson JunctionsUT .......................................................................................... 23

TU4.2.2UT TUMulticore ProcessorsUT......................................................................................... 24

TU4.2.3UT TUParallel Computer ArchitecturesUT ....................................................................... 25

TU4.2.4UT TUMicro-Electromechanical SystemsUT.................................................................... 25

TU4.2.5UT TUDynamically Reconfigurable Integrated CircuitsUT.............................................. 26

TU4.2.6UT TUField Programmable Gate ArraysUT...................................................................... 28

TU4.2.7UT TUField Programmable Analog ArraysUT ................................................................. 29

TU4.2.8UT TUSystem on a ChipUT .............................................................................................. 30

TU4.2.9UT TUHigh-k Transistor TechnologyUT .......................................................................... 30

TU4.2.10UT TUMultigate Transistor TechnologyUT...................................................................... 31

TU4.2.11UT TUOther Emerging Integrated Circuit TechnologiesUT ............................................. 32
viii 

TU4.2.12UT TURadiation-Hardened Integrated CircuitsUT ............................................................32

TU4.3UT TUTECHNOLOGY RISKSUT ..................................................................................................33

TU4.3.1UT TUFailure MechanismsUT...........................................................................................33

TU4.3.2UT TUNew Potential Risks and Aging PhenomenaUT .....................................................35

TU4.4UT TUREGULATORY IMPACT OF MICROPROCESSORS AND OTHER 

INTEGRATED CIRCUITSUT .............................................................................................38

TU5. COMPUTATIONAL PLATFORMSUT...........................................................................................41

TU5.1UT TUOVERVIEW OF COMPUTATIONAL PLATFORMSUT...................................................41

TU5.2UT TUTECHNOLOGY TRENDSUT ..............................................................................................41

TU5.2.1UT TUProcessor Support for Virtual MachinesUT............................................................41

TU5.2.2UT TUDistributed and Multicore ComputingUT...............................................................41

TU5.2.3UT TUOperating Systems and the Embedded Devices MarketUT....................................42

TU5.3UT TUREGULATORY IMPACT OF ADVANCES IN COMPUTATIONAL 

PLATFORMSUT ..................................................................................................................43

TU6. SURVEILLANCE, DIAGNOSTICS, AND PROGNOSTICSUT...................................................45

TU6.1UT TUOVERVIEW OF SURVEILLANCE, DIAGNOSTICS, AND PROGNOSTICSUT............45

TU6.2UT TUTRENDS IN SURVEILLANCE, DIAGNOSTICS, AND PROGNOSTICS 

SYSTEMSUT........................................................................................................................45

TU6.2.1UT TUBasic MethodsUT ...................................................................................................45

TU6.2.2UT TUPhysics or First-Principle ModelsUT......................................................................47

TU6.2.3UT TUData-Driven ModelsUT ..........................................................................................47

TU6.2.4UT TUNonparametric MethodsUT ....................................................................................49

TU6.3UT TUSTATE OF THE ART OF DIAGNOSTIC AND PROGNOSTIC SYSTEMSUT................49

TU6.3.1UT TURedundant Sensor MonitoringUT...........................................................................50

TU6.3.2UT TUAcoustic Emission AnalysisUT ..............................................................................50

TU6.3.3UT TULoose Parts Monitoring SystemUT.........................................................................50

TU6.3.4UT TUPassive Monitoring with Micro-Electromechanical SystemsUT............................51

TU6.3.5UT TUIntegrated Asset Management SystemUT...............................................................51

TU6.4UT TUREGULATORY IMPACT OF ADVANCES IN SURVEILLANCE, 

DIAGNOSTICS, AND PROGNOSTICSUT ........................................................................53

TU7. HUMAN-SYSTEM INTERACTIONSUT ......................................................................................55

TU7.1UT TUOVERVIEW OF TRENDS IN HUMAN-SYSTEM INTERACTIONSUT..........................55

TU7.2UT TUTHE STATE OF THE ARTUT.............................................................................................57

TU7.2.1UT TUPhysical Interface TechnologyUT ..........................................................................57

TU7.2.2UT TUVirtual RealityUT ...................................................................................................58

TU7.2.3UT TUVideo Display UnitsUT ..........................................................................................63

TU7.2.4UT TUAutomation in SystemsUT......................................................................................63

TU7.2.5UT TUControl Room DesignUT........................................................................................64

TU7.3UT TUREGULATORY IMPACT OF HUMAN-SYSTEM INTERACTIONSUT..........................67

TU8. HIGH-INTEGRITY SOFTWAREUT .............................................................................................69

TU8.1UT TUOVERVIEW OF SOFTWARE TRENDSUT .......................................................................69

TU8.2UT TUSOFTWARE DEVELOPMENT FOR SAFETY CRITICAL APPLICATIONSUT ............69

TU8.3UT TUCOMPUTER SOFTWARE DEVELOPMENT AND THE EMERGENT 

TECHNOLOGY WHICH SUPPORTS ITUT.......................................................................71

TU8.4UT TUREGULATORY IMPACT OF SOFTWAREUT ..................................................................75

TU9. INSTRUMENTATION AND CONTROLS ARCHITECTURES IN NEW PLANTSUT..............77

TU9.1UT TUTRENDS IN DIGITAL ARCHITECTURES IN NUCLEAR POWER PLANTSUT ..........77

TU9.2UT TUEUROPEAN PRESSURIZED REACTORUT......................................................................77
ix 

TU9.2.1UT TUSystem-Level Instrumentation and Controls ArchitectureUT................................ 77

TU9.2.2UT TUInstrumentation and Controls Architecture PlatformsUT....................................... 83

TU9.3UT TUADVANCED PRESSURIZED WATER REACTORUT..................................................... 85

TU9.3.1UT TUSystem-Level Instrumentation and Controls ArchitectureUT................................ 85

TU9.3.2UT TUInstrumentation and Controls Architecture PlatformsUT....................................... 91

TU9.4UT TUECONOMIC SIMPLIFIED BOILING WATER REACTORUT......................................... 93

TU9.4.1UT TUSystem-Level Instrumentation and Controls ArchitectureUT................................ 93

TU9.4.2UT TUInstrumentation and Controls Architecture PlatformsUT..................................... 102

TU9.5UT TUREGULATORY IMPACT OF FULLY DIGITAL INSTRUMENTATION AND 

CONTROLS ARCHITECTURES IN NUCLEAR POWER PLANTSUT......................... 102

TU10. REFERENCESUT....................................................................................................................... 105
This Page Intentionally Left Blank 
xi 

LIST OF FIGURES 

Figure Page 

TU1. Transmitted light spectra through a distributed optical fiber Bragg grating.UT............................... 4

TU2. Ultrasonic thermometry system including a notched waveguide.UT ............................................... 5

TU3. Johnson noise thermometry measurement process block diagram.UT............................................. 7

TU4. Basic components of a gamma thermometer.UT.............................................................................. 7

TU5. FOUNDATION fieldbus networkUT ................................................................................................... 12

TU6. Application-oriented features of PROFIBUS.UT............................................................................. 13

TU7. Three-level layer model with safety communication layer applied to a safety system 

network.UT....................................................................................................................................... 14

TU8. Illustration of black channel implementation.UT ............................................................................. 14

TU9. Wireless protocol coverage.UT ........................................................................................................ 15

TU10. Gate leakage has increased 100-fold in the last three generations of transistorsUT......................... 31

TU11. One concept for transistors of the futureUT ..................................................................................... 32

TU12. Hot carrier injection degradation mechanism observed in MOSFETs.UT ....................................... 34

TU13. A simple model of an ARINC 653 partitioned systemUT................................................................ 42

TU14. Block diagram showing the integration of surveillance, diagnosis, and prognosis modules 

in a nuclear power plant.UT.............................................................................................................. 46

TU15. Group method of data handling (GMDH) model that minimizes the error yUB

measUB – yUBpredUB for 

the case of m-inputs {xUB

1UB, xUB2UB, ... , xUBmUB}.UT.......................................................................................... 48

TU16. Comparison of the measured (–) and model-predicted (+) values of the pressurizer level 

signal (%) during start-up of a pressurized-water reactor.UT........................................................... 48

TU17. Asset management as part of life-cycle management (LCM) strategy.UT....................................... 52

TU18. Equipment condition monitoring plan proposed by EPRI.UT.......................................................... 53

TU19. Lungmen Nuclear Power Project digital instrumentation and controls system design 

process.UT ........................................................................................................................................ 56

TU20. Overview of the CREATE systemUT............................................................................................... 60

TU21. Layout Tool with the model library to the left, from which objects can be dragged into the 

sceneUT ............................................................................................................................................ 60

TU22. Distance measurement tool in action.UT.......................................................................................... 61

TU23. Evaluation of label legibility showing the height of the text and calculated range of 

legibilityUT....................................................................................................................................... 61

TU24. Virtual control roomUT .................................................................................................................... 62

TU25. Lungmen plant simulator—a replica of the main control roomUT .................................................. 63

TU26. Different types of minimum-inventory HSIs.UT.............................................................................. 67

TU27. U.S. Evolutionary Pressurized Reactor instrumentation and controls architecture.UT .................... 78

TU28. Block diagram of Olkiluoto-3 Priority and Actuation Control System (PACS) moduleUT ............ 79
xii 

TU29. The monitoring and service interface (MSI) module forms a logical boundary 

between the rest of the safety system and the nonsafety interfaces.UT ............................................ 82

TU30. Overall architecture of the Advanced Pressurized-Water Reactor instrumentation and 

controls systemUT............................................................................................................................. 86

TU31. Communication network between the human-system interface system and other systems.UT........ 89

TU32. Typical configuration of the Mitsubishi Electric Total Advanced Controller platform.UT.............. 92

TU33. Reactor protection system functional blockUT................................................................................. 96

TU34. Economic Simplified Boiling Water Reactor sensors and power diversityUT ................................. 100

TU35. Triple modular redundant architecture of the Tricon PLC system.UT.............................................. 103
xiii 

LIST OF TABLES 

Table Page 

TU1. Failure mechanisms occur at different times in product lifeUT ....................................................... 34

TU2. Assessment of the state of maturity for diagnostic (D) and prognostic (P) technologiesUT............ 49

TU3. Example formalisms for digital safety systems developmentUT ..................................................... 70

TU4. Software development process modelsUT........................................................................................ 74

TU5. Differences in instrumentation and controls among the different European/Evolutionary 

Pressurized Reactor designsUT ........................................................................................................ 77

TU6. Economic Simplified Boiling Water Reactor hardware/software diversity architectureUT............. 94
This Page Intentionally Left Blank 
xv 

EXECUTIVE SUMMARY 

The U.S. Nuclear Regulatory Commission (NRC) Digital System Research Plan forms the framework 

for identifying research areas that the NRC pursues to update the tools used in assessing the safety of 

digital instrumentation and controls (I&C) applications in U.S. nuclear power plants (NPPs). The 

NRC Digital Research Plan for FY 2000–FY 2004TPD

3

DPT identified emerging technologies as an area of 

research. This includes areas that have been shown to be likely to be applied in the future and areas 

that have the potential to raise safety issues but have not been addressed. By becoming informed of 

emerging I&C technology and applications, NRC will be better prepared to make future regulatory 

decisions in these areas. 

Oak Ridge National Laboratory (ORNL) has been tasked to perform the emerging technologies study, 

the first report of which was published in March 2003 as NUREG/CR-6812, Emerging Technologies 

in Instrumentation and Controls. The second report was published in January 2006 as 

NUREG/CR-6888, Emerging Technologies in Instrumentation and Controls: An Update.

Compilation of this third report in the series generally follows the pattern established in the two 

previous NUREG/CRs of reviewing advances in several technology focus areas. Based on the results 

of the program review in FY 2006, in which the focus of the study was redirected to include digital 

I&C in new plants, the focus areas were slightly modified to include I&C architectures in new plants. 

Thus, the focus areas used for this third NUREG/CR in the series are the following: (1) sensors and 

measurement systems, (2) communications media and networking, (3) microprocessors and other 

integrated circuits, (4) computational platforms, (5) surveillance, diagnostics, and prognostics, 

(6) human-system interactions, (7) high-integrity software, and (8) I&C architectures in new plants. 

Findings in these areas are summarized below. 

For the “sensors and measurement systems” focus area, the key regulatory issues include response 

time requirements; accuracy of the instrumentation, which can enable applicants to argue for reduced 

operating margins; credit that can be taken for online sensor diagnostics capability or inherent lack of 

drift of a sensor; and qualification issues associated with new sensor technologies, such as opticalfiber-based sensors. Use of sensors with inherent drift-free characteristics, for example, can eliminate 

the need for calibration. Of the sensors reviewed for this focus area, the Johnson noise thermometer is 

the only one whose continued development can potentially eliminate the need for manual calibration. 

However, widespread commercial application of the method in NPPs is still limited. In the absence of 

such techniques for online sensor monitoring, methods such as cross calibration will continue to 

afford the best means to justify the need for increasing calibration intervals. Current methods of 

verifying an instrument’s performance include routine calibrations, channel checks, functional tests, 

and response time tests. Standards such as ANSI/ISA-67.06.01 provide the nuclear power industry 

with guidelines for performance monitoring of safety-related instruments. This ISA standard provides 

a step-by-step guide for establishing the acceptance criteria for a given instrument signal. Institute of 

Electrical and Electronics Engineers (IEEE) Std. 338-2006, “IEEE Standard Criteria for Periodic 

Surveillance Testing of Nuclear Power Generating Station Safety Systems,” provides criteria for the 

periodic testing of nuclear power generating station safety systems. It appears that, in general, the 

sensing technologies in the nuclear power industry represent adaptations of well-established 

measurement concepts, and “new” sensors are typically evolutionary rather than revolutionary in 

nature. It appears also that revisions of current guidelines and standards are keeping pace with these 

incremental developments in sensor technology. 

For the “communication and networking” focus area, the review showed that advances in digital 

communication systems in general have focused on boosting data transmission speeds, developing 

more robust protocols, error correction and encryption techniques, and (for wireless systems) spread 

spectrum (SS) techniques (direct sequence, frequency hopping, time hopped, chirp). SS radio 

communications techniques have long been favored by the military because signals are hard to jam 
xvi 

and are difficult for an enemy to intercept. However, SS techniques are gaining in popularity in 

industrial and commercial applications due to their advantages in transmitting data using three 

license-free bands known as the industrial, scientific, and medical bands. In general, use of digital 

communication systems in NPPs lags considerably behind that in nonnuclear systems due to the 

stringent requirements these systems have to comply with to be acceptable for NPP applications. 

Gen III and III+ plants are expected to bridge this gap somewhat with their extensive application of 

digital I&C. I&C architectures in new plants will make extensive use of digital communication, both 

between safety systems and between non-safety- and safety-related systems. One of the more 

significant regulatory implications here is maintaining not only physical and electrical independence 

but also data independence between safety and nonsafety systems, thereby guaranteeing that a 

transmission error in one channel or division will not cause the failure of another channel or division. 

The Interim Staff Guidance DI&C-ISG-04 offers good guidance in this regard.TPD

4

DPT The independence 

issue is not so easily resolved with regard to wireless communications systems in NPPs. Howlader et 

al.TPD

5

DPT have developed the technical basis for regulatory guidance on implementing wireless 

communications in NPPs. The application of wireless systems are likely to be limited in the 

foreseeable future to non-safety-related diagnostics and maintenance systems, inventory management 

systems, and voice and data communications to employees and field crews. 

For the “microprocessors and other integrated circuits” focus area, the review findings suggest that 

the growing system complexity of semiconductor devices could make it more difficult to guarantee 

delivering future integrated circuit (IC) hardware free of errors. In addition, the successful 

development of high-k transistor ICs and the potential for multigate transistor ICs could revolutionize 

the IC industry but could also introduce new aging phenomena, higher sensitivity to environmental 

conditions (e.g., temperature and radiation), and other issues related to qualification methodologies. 

Failure modes and mechanisms for both current and emerging digital I&C technologies need to be 

characterized to assess whether current defense-in-depth strategies will need to be updated and 

whether any new failure modes can cause unforeseen or unknown system responses. This is 

especially important in light of fully digital I&C system upgrades in Gen III plants, and the potential 

for advanced digital I&C application in Gen III+ and IV plants in the future. An understanding of 

failure modes at the system level [e.g., programmable logic controllers (PLCs)] is the goal with 

regard to application in safety systems. However, such data may not be readily available, and an 

understanding of failure modes at the component level may be necessary to develop a failure data 

integration framework from module level to system level, contributing to an understanding of how a 

component level failure relates to the failure at the digital I&C system level. In addition to 

characterizing failure modes to inform the regulatory process, the use of “complex” devices such as 

field programmable gate arrays (FPGAs) in safety systems also needs to be carefully reviewed 

because such devices have the potential to be reconfigured, and reconfigurability increases reuse and 

the potential for adversely affecting the execution of a safety function. Use of FPGAs in safety 

systems also brings into focus the issue of how much verification and validation (V&V) should be 

required. 

In the “computational platforms” focus area, the review concluded that complex computing platforms 

(e.g., those using multicore processors) and operating systems are more likely to be used in control 

and information display applications than in safety applications because of the much more rigorous 

demand for V&V in the latter. Safety-critical applications typically assign functions to 

deterministically scheduled time slots, dividing the single CPU among them so that the computer is 

doing just one function at a time. For many safety system platforms developed for new plants as well 

as upgrades, an operating system platform such as Windows is likely to be used to run an engineering 

tool that automatically generates the application software for downloading into the safety-related 

subsystem modules. This automated process eliminates human translation errors. However, the issue 

of a more rigorous V&V for the engineering tool becomes more significant because of the safetyrelated application. 
xvii 

Several nuclear plant upgrades and new plants will use PLC-based platforms, some of them with 

embedded application-specific integrated circuits (ASICs). Some of these platforms have already 

been approved (e.g., TELEPERM XS). Thus, there is some experience base with regard to reviewing 

digital I&C safety systems for compliance with regulations. However, continued awareness of 

progress in this technology is recommended. Operating systems provide the fundamental interface 

between software and hardware in most digital applications. Thus, their performance and reliability 

characteristics should be well understood. 

The computational platforms for digital-based systems in NPPs cover an extraordinarily broad range 

of devices. At the simplest end, a digital device in a safety system might consist of a few logic 

devices in a PLC or a few elements on an ASIC. The “program” being executed is almost as simple as 

an analog device “run when you are turned on.” The regulatory question then becomes, when does a 

digital device become so simple that it no longer comes under the heading of digital computer? 

Regulatory guidance for such systems and devices [e.g., FPGAs, complex programmable logic 

devices (CPLDs)] that are halfway between “simple” and “complex” is currently not as well defined. 

For example, Position 8 of Section 2, “Command Prioritization,” of the Interim Staff Guidance 

DI&C-ISG-04 requires a priority module design to be fully (i.e., 100%) tested. This refers to proofof-design testing, not to individual testing of each module and not to surveillance testing. If the 

priority module is designed using a CPLD or a device of similar complexity, it may be very difficult, 

if not impossible, to prove that such a device has been fully tested. In this case, the authors have 

suggested guidance for V&V that still provides reasonable assurance of a reliable system, to the same 

level as a software-based system. 

For “surveillance, diagnostics, and prognostics,” we reviewed the literature to estimate the general 

state of maturity of this technology focus area in the nuclear industry. Surveillance and diagnostics 

techniques have been used for many different applications, such as loose-parts detection, core barrel 

motion monitoring, rotating machinery condition monitoring, instrument response time 

measurements, predictive analysis of failures in sensors and sensor lines, and motor current signature 

analysis. However, advances will have to be made in several areas to move from periodic inspection 

to online monitoring for condition-based maintenance and eventually prognostics. These areas 

include sensors, better understanding of measurement in the plant environment (e.g., what and how to 

measure), enhanced data interrogation, communication and integration, new predictive models for 

damage/aging evolution, system integration for real-world deployments, and integration of enhanced 

condition-based maintenance/prognostics philosophies into new plant designs. 

Automatic surveillance offers tremendous new opportunities for plants to operate more reliably, test 

more frequently, reduce risk of latent failures, reduce maintenance costs, and reduce worker 

exposure—all of this at the low cost of digital monitoring systems. The issues from a regulatory 

standpoint are mainly concerned with when the surveillance system is applied to a safety system and 

the surveillance performs a required function under regulatory control based on Regulatory Guide 

1.118. A number of fundamental questions emerge, as follows. (1) Are there any subjective 

monitoring criteria that an expert adds to a manual surveillance that are lost in the automated 

surveillance system? (2) Are the systems being monitored and their failure modes easy to recognize? 

(3) Are the surveillance system’s failures easy to recognize? (4) Can the operator accurately tell the 

difference between the failure of the surveillance system and the failure of the device it is 

monitoring? (5) Does the presence of the automated surveillance system affect the reliability of the 

safety function? (6) How can the surveillance function be protected against a software fault that leads 

to a common cause failure to detect a failed protection system? The regulatory authority is currently 

struggling with the implications of diversity and defense-in-depth (D3) regarding digital protection 

functions. Logically, the same concern can be applied to surveillance software. The issue for 

diagnostic software is more difficult because diagnostic software is typically more complex in 
xviii 

concept than a safety system. The issue from a regulatory point of view is not clear. D3 issues for 

surveillance systems have not been adequately considered to date. 

For the “human-system interactions” focus area, the review found that control room (CR) design has 

rapidly changed as more computerization and automation have been incorporated. Advanced control 

room (ACR) concepts are being implemented in the commercial nuclear industry for new plant 

designs. Use of advanced human-system interface (HSI) technologies in ACRs has more implications 

with plant safety because implementation for safety systems affects the operator’s overall role 

(function) in the system, the method of information presentation, the ways in which the operator 

interacts with the system, and the requirements on the operator to understand and supervise a more 

fully integrated main CR HSI. The review found that there are many evolving design and evaluation 

tools that can optimize the design of human interfaces and speed up their evaluation. All are based on 

computer software technologies. Many of these tools are being developed outside of the nuclear 

power industry. It is widely accepted that poor human factors engineering (HFE) in systems design 

contributes to poor human performance, increased errors, and reduced human reliability. In addition, 

under degraded or emergency conditions poor HFE design can delay or prevent corrective action by 

plant operators. The perfect CR layout, with attendant perfect operator interaction and allocation of 

human-machine function, has not yet been developed. Even if such an ACR had been developed, the 

tools to confirm its performance capabilities have not yet been developed. It is therefore in the interest 

of improving and verifying the efficacy of ACRs that research continues in the three major areas of 

tool development: measurement tools for physical human interface; human-machine interface and 

interaction design criteria and guidance, especially for allocation of functions in highly automated 

CRs; and functional simulation modeling, including human performance modeling. 

In the “high-integrity software” focus area, the review found considerable advances in software 

engineering since the last update but that these advances have, in general, not kept pace with 

advances in hardware. Software cannot typically be proven to be error-free and is therefore 

considered susceptible to common-cause failures (CCFs) if identical copies of the software are 

present in redundant channels of safety-related systems. At the heart of mitigating strategies to cope 

with CCFs is a judicious use of various diversity measures and an analysis of how each diversity 

measure can cope with particular categories of CCFs. NUREG/CR-6303 identifies the following six 

categories of diversity: (1) design diversity, (2) equipment diversity, (3) functional diversity, 

(4) human diversity, (5) signal diversity, and (6) software diversity. The review concluded that the 

use of diversity to protect against CCFs in software design is not likely to change. However, a great 

deal of effort can go toward advanced software development techniques that reduce the likelihood of 

software faults in a digital safety function, make the software less costly, and make the software 

easier to review and license for use. The conventional tools of the software development cycle using 

tools such as the waterfall model are also used for nuclear software development. The process is cost 

intensive and relies to a large extent on human involvement at each step of the waterfall to inspect 

and test results and to verify and validate that the requirements have been met. The goal of high 

integrity software developments is to improve the process by automating and systematizing the 

methods. The range of advanced software techniques that are being developed includes methods that 

automate design steps and report generation, organize the work in new ways that tend to make errors 

less likely, or automate testing and V&V. It is no longer just the computer program that runs on the 

device that affects quality, but the much larger system of software used to develop it. The challenge 

for regulatory bodies is to find ways to review and accept the new strategies using complex, 

automated design and development tools. In this regard, PRAXIS, a British company, claims to have 

developed a highly reliable and provable code based on a National Security Agency funded project.TPD

6

DPT

The software has approximately 10,000 lines of code. Perhaps regulatory bodies may want to review 

the procedures used to develop such claimed reliable code and develop review procedures aimed at 

ensuring highly reliable code in the NPP environment. 
xix 

For the “I&C architectures in new plants” focus area, the I&C features for three new reactor designs 

were reviewed—the Advanced Pressurized-Water Reactor by Mitsubishi Heavy Industries; the U.S. 

Evolutionary Pressurized Reactor by AREVA NP; and the Economic Simplified Boiling Water 

Reactor by GE-Hitachi. The review indicated that these designs use fully digital and networked 

architectures. Some safety-related modules and subsystems in the plants reviewed include ASICs, 

FPGAs, or CPLDs. While the current regulatory process does an excellent job of ensuring reliable 

safety system designs, issues whose resolution can enhance the regulatory process for digital systems 

still remain. These include (1) the need for a complete characterization of failure modes for digital 

systems; (2) determining how much V&V should be required for systems that are halfway between 

“simple” (e.g., binary ON, OFF, and/or a small number of combinatorial logic) and “complex” [e.g., 

microprocessor- and/or software-based (i.e., must V&V be required to the same level as a computerbased system?)]; (3) determining how the surveillance function can be protected against a software 

fault that leads to a common cause failure to detect a failed protection system; and (4) determining 

how much credit should be given to an online diagnostic system, which in itself could be more 

complex than a simple protection system function. 
This Page Intentionally Left Blank 
xxi 

ABBREVIATIONS AND ACRONYMS 

ACR advanced control room 

ACRS Advisory Committee on Reactor Safeguards 

ADC analog-to-digital converter 

ANN artificial neural network 

APWR Advanced Pressurized-Water Reactor 

AR auto-regression 

ASIC application-specific integrated circuit 

AWGN additive white Gaussian noise 

BE broadband engine 

BER bit error rate 

BMI brain-machine interface 

BOP balance of plant 

BPU bypass unit 

BWR boiling-water reactor 

CAD computer aided design 

CAVE Cave Automatic Virtual Environment 

CB control building 

CCF common-cause failure 

CDMA code division multiplexing access 

CIM communication interface module 

CMF common-mode failure 

CMFDD condition monitoring failure detection and diagnostics 

CMM capability maturity model 

CMMI capability maturity model integration 

CMOS complementary metal-oxide semiconductor 

COSS computerized operator support system 

CPF communication profile family 

CPU central processing unit 

CR control room 

CRC cyclic redundancy checking 

CSCW computer-supported cooperative work 

D3 diversity and defense-in-depth 

DAC digital-to-analog converter 

DARPA Defense Advanced Research Projects Agency 

DAS diverse actuation system 

DCIS distributed control and information system 

DCS data communication system 

DOE U.S. Department of Energy 

DPS diverse protection system 

DRAM dynamic random access memory 

DSP digital signal processing/processor 

DTM digital trip module 

ECA elemental computing arrays 

ECCS emergency core cooling system 

EdF Electricité de France 

EEPROM electrically erasable programmable read-only memory 

EOS electrical over stress 
xxii 

EPR European Pressurized Reactor (or Evolutionary Pressurized Reactor for the U.S. 

version) 

EPRI Electric Power Research Institute 

EPROM erasable programmable read-only memory 

ESBWR Economic Simplified Boiling Water Reactor 

ESF engineered safety features 

ESFAS engineered safety features actuation system 

F-ROM flash electrically erasable programmable read-only memory 

FBG fiber (optic) Bragg grating 

FDI fault detection and isolation 

FEC forward error-correction coding 

FFT fast Fourier transform 

FIT failures in time 

FPAA field programmable analog array 

FPGA field programmable gate array 

FRAM ferroelectric random access memory 

GaAs gallium arsenide 

GE-H General Electric-Hitachi 

GFlops Giga Floating point operations per second 

GIS geographical information system 

GMDH group method of data handling 

HBS hard wired backup system 

HCI hot carrier injection 

HCU hydraulic control unit 

HFE human factors engineering 

HMI human-machine interface 

HSE high-speed Ethernet 

HSI human-system interface 

HVAC heating, ventilation, and air conditioning 

I&C instrumentation and controls 

I/O input/output 

IC integrated circuit 

ICA independent component analysis 

IEC International Electrotechnical Commission 

IEEE Institute of Electrical and Electronics Engineers 

IFE Norwegian Institute for Energy Technology 

ISO International Organization for Standardization 

ITRS International Technology Roadmap for Semiconductors 

JNT Johnson noise thermometry 

LAN local area network 

LAS link active scheduler 

LCM life-cycle management 

LD&IS leak detection and isolation system 

LDU loop diagnostic unit 

LED light-emitting diode 

LOS line of sight 

LMNPP Lungmen Nuclear Power Project 

LOOP loss of offsite power 

LPMS loose parts monitoring system 

LPRM local power range monitor 

LWR light-water reactor 
xxiii 

MAN metropolitan area network 

MCC main control console 

MCR main control room 

MEM micro-electromechanical 

MEMS micro-electromechanical systems 

MHI Mitsubishi Heavy Industries 

MIMD multiple-instruction, multiple-data 

MIMO multi-input multi-output 

MIS metal-insulator-semiconductor 

MISCIC memory-intensive self-configuring integrated circuit 

MOS metal-oxide semiconductor 

MPSoC multiprocessor systems on a chip 

MSI monitoring and service interface 

MSIV main steam line isolation valve 

NBTI negative bias temperature instability 

N-CIM non-safety-related CIM 

N-DCIS non-safety-related DCIS 

NEMS nanoelectromechanical system 

NMOS negative metal-oxide semiconductor 

NMS neutron monitoring system 

NPP nuclear power plant 

NRC U.S. Nuclear Regulatory Commission 

NSSS nuclear steam supply system 

NUMAC Nuclear Measurement Analysis and Control 

OFDM orthogonal frequency division multiplexing 

OFDR optical frequency domain reflectometry 

OLU output logic unit 

ORNL Oak Ridge National Laboratory 

PAC priority actuation and control 

PAN personal area network 

PAS process automation system 

PC personal computer 

PCI peripheral component interconnect (PC bus) 

PCMS plant control and monitoring system 

PER packet error rate 

PICS process information and control system 

PLC programmable logic controller 

PM preventive maintenance 

PMOS positive metal-oxide semiconductor 

PPE power processing element 

PRNM power range neutron monitor(ing) 

PROM programmable read-only memory 

PS protection system 

PSMS protection and safety monitoring system 

PWR pressurized-water reactor 

Q-CIM safety-related CIM 

Q-DCIS safety-related DCIS 

QDS qualified display system 

RAM random-access memory 

RB reactor building 

RCSL reactor control, surveillance, and limitation system 
xxiv 

RFID radio-frequency identification (RF technology for tracking items and personnel) 

RMS root mean square 

RMU remote multiplexing unit 

ROM read-only memory 

RPS reactor protection system 

RSET redundant sensor estimation technique 

RSR remote shutdown room 

RSS remote shutdown station 

RTD resistance temperature detector 

RTIF reactor trip and isolation function 

RTS reactor trip system 

SAS safety automation system 

SCL safety communication layer 

SCO station containment outage 

SDR software defined radio 

SDRAM synchronous dynamic random access memory 

SEE single event effect 

SEL single event latch-up 

SEU single event upset 

SICS safety information and control system 

SiGe silicon germanium 

SIMD single-instruction, multiple-data 

SLS safety logic system 

SNR signal-to-noise ratio 

SoC system on a chip 

SOI silicon-on-insulator 

SPE synergistic processing element 

SPTM suppression pool temperature monitoring 

SRAM static random access memory 

SRNM source range neutron monitor 

SS spread spectrum 

TDDB time-dependent dielectric breakdown 

TLU trip logic unit 

TMR triple modular redundant 

TSC technical support center 

TSS task support system 

TXP TELEPERM XP 

TXS TELEPERM XS 

UNII unlicensed national information infrastructure 

US-EPR U.S. Evolutionary Pressurized Reactor 

USB universal serial bus 

UWB ultra-wideband 

V&V verification and validation 

VDU video display unit 

VHDL Very High Integration Hardware Description Language 

VLU voter logic unit 

VM virtual machine 

VPN virtual private network 

VR virtual reality 

WAN wide area network 

WDP wide display panel 
xxv 

Wi-Fi wireless fidelity 

ZRAM zero-capacitor random access memory 
This Page Intentionally Left Blank 
1 

1. INTRODUCTION 

1.1 BACKGROUND 

This report provides an update on the instrumentation and controls (I&C) technology surveys 

documented in NUREG/CR-6812 and NUREG/CR-6888. This report is the third in this series of 

NUREG/CRs designed to provide periodic reports on the status of specific technologies that have 

potential applicability for safety-related systems in nuclear power plants (NPPs) and pose emerging 

research needs. NUREG/CR-6812 provided a broad-brush overview of I&C technologies and served 

as the baseline for the series of periodic reports specified in the U S. Nuclear Regulatory Commission 

(NRC) Plan for Digital Instrumentation and Control (SECY-01-0155). NUREG/CR-6888 provided 

an update on the state-of-the-art in the technology areas identified in the previous report. 

The primary objective of the NRC Emerging Technologies project is to assist NRC in the 

identification of key research areas on emerging technologies within the I&C field that may become 

important in the future. The Emerging Technologies study in effect provides “intelligence” pertaining 

to new, improved, and/or advanced I&C equipment and systems that are being studied or developed 

by vendors for use in reactor plant designs. This will enable informed regulatory judgments to be 

made regarding their usage. This study also presents well known technologies which have potential 

for use but have not yet been widely deployed in NPPs. The output of the study is provided as a series 

of NUREG/CRs published about every 2–3 years. 

1.2 SCOPE OF STUDY 

Eight technology focus areas were reviewed: (1) sensors and measurement systems, 

(2) communications media and networking, (3) microprocessors and other integrated circuits (ICs), 

(4) computational platforms, (5) surveillance, diagnostics, and prognostics, (6) human-system 

interactions, (7) high-integrity software, and (8) I&C architectures in new plants. For the latter, we 

reviewed the I&C features for several new reactor designs [e.g., the U.S. Evolutionary Pressurized 

Reactor (US-EPR) by AREVA NP and the Advanced Pressurized-Water Reactor (APWR) by 

Mitsubishi Heavy Industries (MHI)]. 

1.3 RESEARCH APPROACH 

The research approach taken in this survey closely follows that used in the previous reports. The 

multidisciplinary expertise at Oak Ridge National Laboratory (ORNL) and the University of 

Tennessee was employed to review the state-of-the-art of the technology focus areas covered in the 

study. Investigations were conducted that consisted of literature reviews (in particular, recent 

scientific and technical journals), Internet searches, vendor contacts, and discussions with technology 

experts. Input was also solicited from nuclear industry representatives such as the Electric Power 

Research Institute (EPRI).On the basis of the results from these combined investigations, the study 

provides a summary update on each of these technologies. 

1.4 STRUCTURE OF REPORT 

One chapter is devoted to each focus area. Each chapter is in three main sections: the first section 

provides a summary of the findings for that focus area; the second section provides details of the 

review for that focus area; and the third section provides a discussion of the regulatory impact. 
This Page Intentionally Left Blank 
3 

2. SENSORS AND MEASUREMENT SYSTEMS 

2.1 SENSORS AND MEASUREMENT SYSTEMS OVERVIEW 

The measurement systems (i.e., the sensing element, transducer, and signal-conditioning electronics) 

in currently operating NPPs have not changed appreciably since their original design and are 

primarily based on conventional instruments and methods. The principal variables measured for 

safety-related applications continue to be neutron flux, temperature, pressure, radiation, flow, 

position, and level. Although dated, the Nuclear Power Reactor Instrumentation Systems Handbook,TPD

7

DPT

published in 1973 by the U.S. Atomic Energy Commission, still provides a good general outline of 

the sensing systems used in currently operating NPPs. 

The sensing technologies in the nuclear power industry represent adaptations of well-established 

measurement concepts to the specific requirements of NPP environments as opposed to unique 

concepts specifically developed for the nuclear industry. Therefore, their advantages, disadvantages, 

deployment requirements, and performance characteristics can be predicted with reasonable 

confidence based on their deployment history in industrial environments. 

Distributed fiber-optic-based Bragg grating thermometry appears to be well suited for monitoring the 

health of the major electromechanical components in the nuclear energy production process. 

Ultrasonic technologies also may be near the stage where they may become more widely deployed 

in-vessel. Higher temperature ultrasonic transducers appear to be coming of age, allowing for signal 

conversion within the pressure boundary, and complex signal processing has become readily available 

with the advent of modern digital electronics. 

As a promising temperature measurement technique, Johnson noise thermometry (JNT) offers a 

technology of significant potential value to the nuclear power industry. While little technical progress 

has been made in developing industrial-quality JNT instruments, the technology seems to have stalled 

at a level where only a few years of concerted effort would be necessary to achieve a widely 

deployable technology. 

Gamma thermometers are now coming into wide use as the long-term baseline power measurement 

technology in boiling-water reactor (BWR) cores, replacing traveling miniature fission chambers. 

Gamma thermometers have also been used for local power monitoring in commercial pressurizedwater reactors (PWRs) since the early 1980s. While the technology is roughly 40 years old and is in 

the instrumentation design basis for the Economic Simplified Boiling Water Reactor (ESBWR), 

gamma thermometers remain an emerging technology not yet having achieved widespread, long-term 

deployment. 

Type-N thermocouples were developed in the late 1970s through the 1980s as a more stable 

replacement for the widely deployed Type-K. The new generation of NPPs now under consideration 

appears more likely to adopt the more stable thermocouple type because they do not have existing 

instrumentation amplifiers that would need to be replaced to take advantage of the increased stability. 

2.2 DETAILS OF SELECTED SENSORS 

This section briefly describes operating principles and performance advantages of the sensors 

identified in the overview. 
4 

2.2.1 Distributed Fiber-Optic Bragg Thermometry 

Distributed fiber-optic Bragg thermometry is based upon a series of Bragg gratings arranged along 

the core of a single-mode optical fiber (see XFigure 1X). Fiber Bragg grating (FBG) was first 

demonstrated using visible argon-ion laser.TPD

8

DPT Later, Meltz and colleagues improved the technique to 

its current form by incorporating coherent UV radiation.TPD

9

DPT The temperature dependence of the Bragg 

wavelength of an FBG element originates from the thermal expansion of the fiber, which results in 

detectable variation in the optical index of the core. Although the FBGs were known to respond to 

variations in multiple parameters such as load, strain, vibration, and temperature, the first 

demonstration of the technique as a temperature sensor was done by Kersey and Berkoff.TPD

10DPT 

Figure 1. Transmitted light spectra through a distributed optical fiber Bragg grating. 

The primary advantages of distributed fiber-optic Bragg thermometry are that the sensor is 

nonconductive, allowing for deployments in high electromagnetic field environments such as pump 

motors and turbines, and that many sensors can be configured along a single path enabling the 

acquisition of a distributed temperature map with a single readout system. This would enable 

applications such as direct observation of the temperature profile across the primary piping instead of 

relying on single radius sampling. 

The simplest readout technique for a limited number of gratings along a fiber begins by launching a 

band [range of wavelengths such as from a light-emitting diode (LED)] of light into the optical fiber. 

Each grating reflects a specific wavelength within the band. The particular wavelength reflected is 

determined by the Bragg grating period, with each individual grating having a slightly different 

spacing. Temperature causes the grating period to shift both by thermal expansion and by change in 

the refractive index. A shift in the reflected wavelength therefore corresponds to a shift in the 

temperature of a particular Bragg grating. 

Another readout technique is optical frequency domain reflectometry (OFDR), which can be used to 

measure the signal from many (thousands of) individual gratings along a fiber.TPD

11DPT OFDR is an 

interferometric technique which requires a coherent, adjustable-wavelength light source. Tunable 

lasers remain somewhat expensive and have more limited lifetime than simple, wideband light 

sources. Consequently OFDR would only be the preferred readout technique for large sensor arrays. 

Distributed fiber-optic Bragg thermometers have been demonstrated to function briefly in high (core 

type) radiation environments and much longer in more moderate radiation environments.TPD

12DPT–

DDTD

14DTP

 The 

optics and electronics for distributed fiber-optic Bragg thermometers can be located hundreds of 

meters from the sensing elements, allowing placement in well-controlled environments at NPPs. Also, 

Bragg gratings in standard communication type optical fibers bleach out upon exposure to combined 

high temperatures and high-radiation fields. To mitigate bleaching of Bragg gratings, less common 

custom optical fibers expressly designed for higher-temperature, higher-dose applications must be 

deployed. This contrasts with resistance temperature detectors and thermocouples, where devices 

suitable for nuclear power application are substantially the same as for nonnuclear deployments. 
5 

Distributed fiber-optic Bragg grating thermometry is now commercially available with the remaining 

primary limitation for deployment in nuclear power safety systems being the requirement to qualify 

the system components. 

2.2.2 Ultrasonic Wireline Thermometry 

Although the field of ultrasonic temperature measurement has many embodiments, the wireline, 

pulse-echo ultrasonic sensor is especially suitable to reactor-vessel temperature measurement due to 

its rugged nature. Experimental studies in reactor safety using ultrasonic wireline thermometry were 

performed as early as the 1960sTPD

15DPT within an environment as severe as within molten corium.TPD16DPT A 

review of the technology stressing nuclear power applications was published in 1972.TPD

17DPT More recently 

Lynnworth provided a detailed overview of ultrasonic probe temperature sensors.TPD

18DPT Progressive 

development of high-temperature materials, high-speed electronics, and signal processing methods 

has pushed the technology forward. While ultrasonic wireline thermometry systems are currently 

available commercially, the technology has not been widely deloyed in U.S. NPPs and therefore 

remains an emerging technology. 

Ultrasonic wireline thermometry is based upon the change in the velocity of sound within a wire with 

temperature. The speed of sound in a wire varies with its elastic modulus and density, as described in 

Eq. X(1)X. Although both parameters are temperature dependent, the temperature effect on elastic 

modulus dominates by about an order-of-magnitude over that of density, which causes sound velocity 

v to decrease with increasing temperature. 

( )

( ) ( ) TY T

v T

ρ = , (1) 

where Y represents Young’s modulus and ρ represents density, all as a function of temperature T. 

Ultrasonic wireline temperature measurement begins by launching an extensional wave down a 

waveguide. The return time of reflections of the launched wave pulse are then recorded. The wireline 

contains a series of notches, and the time difference between reflections from each of the notches is 

indicative of the temperature between the notches (see XFigure 2X). 

30 m

TA TB

Remendur

(48% Co, 47.6% Fe,

4% V, 0.4% Mn)

Expansion Band

Transducer

Electronics

Figure 2. Ultrasonic thermometry system including a notched waveguide. 

2.2.3 Johnson Noise Thermometry 

Measurement of the true coolant temperature is a primary NPP safety system requirement. The harsh 

environment of the NPP causes all known thermometer elements to drift. Consequently, the sensors 

require periodic recalibration, and operating margin is required to be left due to potential temperature 

measurement drift. JNT is an approach that potentially eliminates this problem. JNT was first 
6 

investigated about 50 years ago for high temperature measurementsTPD

19DPT and later used for in-core 

temperature measurement in reactor UexperimentsU.TPD

20DPT However, it has remained largely experimental 

until recently. The technology is finally progressing to the point where commercial applications could 

be possible in a few years. 

Johnson noise is a first-principles representation of temperature. Fundamentally, temperature is 

merely a convenient representation of the mean kinetic energy of an atomic ensemble. Because 

Johnson noise is a fundamental representation of temperature (rather than a response to temperature 

such as electrical resistance or thermoelectric potential), Johnson noise is immune from chemical and 

mechanical changes in the material properties of the sensor. The nonrelativistic form of the 

relationship between temperature, resistance, and voltage generated is given by the Nyquist 

relationship: 

V k TR f = 4 B Δ 2 , (2) 

where 2 V is the mean squared value of the voltage—also called power spectral density—across a 

resistor of resistance R, kB

BB is Boltzmann’s constant, T is the absolute temperature of the resistor, and 

Δf is the measurement bandwidth. To make a temperature measurement using Johnson noise, the 

frequency response of the total system must be known as well as the resistance. Temperature is then 

computed by dividing the power spectral density of the noise voltage by 4kB

BBR. Because of the 

statistical nature of the voltage measurement, the measured value can be distorted by high noise 

content. The noise level can be reduced by longer integration time of the measurement. 

JNT is best understood as a continuous, first-principles recalibration methodology for a conventional 

resistance-based temperature measurement technique. The traditional method of directly measuring 

temperature from a resistance temperature detector (RTD) has unavoidable, unacceptable drift. JNT 

measurement is applied in parallel to the RTD lead wires of the resistance measurement circuit 

without altering the traditional resistance measurement circuit. 

One of the features of being a first-principles measurement is that Johnson noise does not require 

periodic calibration. Thus, the combined temperature measurement approach achieves the speed and 

accuracy of traditional resistance thermometry while adding the feature of automatic calibration. 

A block diagram illustrating the combined measurement process is shown in XFigure 3X. In the diagram, 

the RTD, which is exposed to process temperature, exhibits both a resistance value and Johnson 

noise. These two signals are separable and thus can be processed independently. The RTD’s 

resistance temperature value is compared with the Johnson noise temperature, and a correction is 

made to the transfer function. This correction can be made quasi-continuously or on a periodic basis 

(daily) depending on the RTD’s drift and target uncertainty values. As shown in XFigure 3X, the output 

of the RTD resistance measurement system with Johnson noise correction periodically applied 

provides a prompt temperature measurement with consistently high accuracy. 
7 

Figure 3. Johnson noise thermometry measurement process block diagram. 

2.2.4 Gamma Thermometers 

While gamma thermometers have existed in some form since the 1950s,TPD

21DPT and indeed the NRC 

approved their use for local power measurement in PWRs in 1982, gamma thermometers are only 

now beginning to emerge into widespread use in commercial NPPs. For example, gamma 

thermometers are currently being proposed for local power range monitor (LPRM) calibration in the 

ESBWR.TPD

22DPTGamma thermometers, however, remain an emerging technology because they have not 

yet achieved widespread, long-term deployment within U.S. commercial NPPs. 

Gamma thermometers (XFigure 4X) function based upon the heating of the sensor assembly by gamma 

rays and the subsequent controlled differential cooling of the sensor body. The temperature 

differential developed along the cooling path is proportional to the rate of heating by the incident 

gamma rays, which is in turn proportional to the local power generation rate during power range 

operation. As shown in XFigure 4. Xone embodiment of the gamma thermometer consists of a stainless 

steel rod with argon-filled annular chambers located at each LPRM fission chamber level. A 

differential thermocouple is embedded in the rod at each chamber location. The thermocouple 

junctions develop a temperature difference proportional to the gamma flux the rod is exposed to. An 

electrical heating element is included within the gamma thermometer to provide an alternate heating 

source for calibration. 

Figure 4. Basic components of a gamma thermometer. 

2.2.5 Type-N Thermocouples 

Type K thermocouples are widely used throughout the commercial nuclear power industry. However, 

they exhibit known thermoelectric instabilities. First, Type K thermocouples exhibit a long-term, 
8 

typically cumulative drift in Seebeck coefficient upon long exposure at elevated temperatures. This 

phenomenon is characteristic of all base metal thermocouples. The phenomenon is mainly due to 

compositional changes caused by oxidation (especially internal oxidation) and neutron 

transmutation.TPD

23DPT Type K thermocouples are also subject to a cyclic shift in the positive leg atomic 

structural configuration (referred to as “short range ordering”).TPD

24DPT Finally, Type K thermocouples are 

subject to a perturbation in the Seebeck coefficient of the negative leg due to magnetic 

transformations of temperature-range-dependent magnetic transformations.TPD

25DPT 

Type N (Nicrosil-Nisil) thermocouples were developed in the 1970s and 1980s as a lower drift 

alternative to other base metal (particularly Type K) thermocouples.TPD

26DPT Having achieved designation 

as a standard thermocouple type by the Instrument Society of America in 1983, Type-N 

thermocouples have been in widespread use in non-nuclear environment for more than 20 years. The 

Nicrosil and Nisil alloys composing Type N thermocouples were developed specifically to overcome 

the instabilities of other base metal thermocouples. Nicrosil and Nisil alloy compositions feature 

increased component solute concentrations (chromium and silicon) in the nickel base to transition 

from internal to surface modes of oxidation and include solutes (silicon and magnesium) which 

preferentially oxidize to form oxygen diffusion barriers.TPD

27DPT Moreover, Type N thermocouples were 

also specifically designed for improved high fluence neutron performance by eliminating all elements 

with high neutron absorption cross sections from the compositions of the thermoelements. 

Type N thermocouples are now widely available commercially at similar cost to other base metal 

thermocouples and with similar values of thermoelectric voltage output. As commercial NPPs attempt 

to reduce the required instrumentation margins in their technical specifications, adoption of Type N 

thermocouples as a general replacement for other thermocouples (specifically Type K) should be 

anticipated. 

2.3 REGULATORY IMPACT OF SENSORS AND MEASUREMENT SYSTEM 

TECHNOLOGIES 

The key regulatory issues associated with sensors and measurement systems in NPPs include 

response time requirements; accuracy of the instrumentation, which can enable applicants to argue for 

reduced operating margins; credit that can be taken for online sensor diagnostics capability or 

inherent lack of drift of a sensor; and qualification issues associated with new sensor technologies, 

such as optical-fiber-based sensors. Use of sensors with inherent drift-free characteristics for 

example, can eliminate the need for calibration. Of the sensors reviewed in this chapter, JNT is the 

only one whose continued development can potentially eliminate the need for manual calibration. In a 

practical application, JNT is best used as a continuous, first-principles recalibration methodology for 

a conventional resistance-based temperature measurement technique. However, widespread 

commercial application of the method in NPPs is still limited. In the absence of such techniques for 

online sensor monitoring, methods such as cross calibration will continue to afford the best means to 

justify the need for increasing calibration intervals.TPF

*

FPT Current methods of verifying an instrument’s 

performance include routine calibrations, channel checks, functional tests, and response time tests. 

Standards such as ANSI/ISA-67.06.01, “Performance Monitoring for Nuclear Safety-Related 

Instrument Channels in Nuclear Power Plants,”TPD

28DPT provide the nuclear power industry with guidelines 

for performance monitoring of safety-related instruments. This ISA standard provides a step-by-step 

guide for establishing the acceptance criteria for a given instrument signal. Institute of Electrical and 

Electronics Engineers (IEEE) Std. 338-2006, “IEEE Standard Criteria for Periodic Surveillance 

Testing of Nuclear Power Generating Station Safety Systems,” provides criteria for the periodic 

 

TP

*

PTIt should be noted that in standards such as ANSI/ISA-67.06.01, cross calibration is considered a valid technique for 

monitoring redundant RTDs but is not acceptable for pressure sensors. 
9 

testing of nuclear power generating station safety systems. The scope includes functional tests and 

checks, calibration verification, and time response measurements. It appears that, in general, the 

sensing technologies in the nuclear power industry represent adaptations of well-established 

measurement concepts, and “new” sensors are typically evolutionary rather than revolutionary in 

nature. It appears also that revisions of current guidelines and standards are keeping pace with these 

incremental developments in sensor technology. 
This Page Intentionally Left Blank 
11 

3. COMMUNICATION MEDIA AND NETWORKING 

3.1 COMMUNICATION MEDIA AND NETWORKING OVERVIEW 

This section presents an overview of digital communication technologies and their application to field 

instrumentation such as sensors, controllers, and actuators. These technologies are widely used in 

industry in wired as well as in wireless platforms. They are beginning to find acceptance in NPPs as 

evidenced by their plant-wide application in Gen III+ power plant designs. However, application of 

wireless communications remains limited to non-safety-related communication, diagnostics, 

inventory/database applications, and wireless local area network (LAN) devices for office use. 

Several trends in wireless communications have the potential to enhance communication systems 

performance in NPPs, but they could also present security and possible safety challenges. In any 

wireless application, the main concerns to be considered are security, reliability, and spectrum 

management. 

Advances in digital communication systems in general have focused on boosting data transmission 

speeds, development of more robust protocols, error correction and encryption techniques, and (for 

wireless systems) spread spectrum (SS) techniques (direct sequence, frequency hopping, time 

hopping, chirp). SS radio communications techniques have been long favored by the military because 

the signals are hard to jam and are difficult for an enemy to intercept. Other advantages of the SS 

signals are increasing resistance to natural interference and jamming (interfering with narrowband 

signals). In general, use of digital communication systems in NPPs lags considerably behind use in 

nonnuclear systems due to the stringent requirements these systems have to comply with to be 

acceptable for NPP applications. Gen III and III+ plants are expected to bridge this gap with their 

extensive application of digital I&C. 

One of the common industrial, wire-based networks is the fieldbus. Fieldbus technology has matured, 

and several variants are available. However, despite its several advantages, including lower 

installation and operation cost, interoperability, fewer penetrations through plant containment, 

improved information accuracy, etc., the use of the technology is still much more prevalent in the 

nonnuclear environment than in the nuclear environment. Two concerns for using fieldbus technology 

in the nuclear industry are (1) the potential for common-cause failures (CCFs) resulting from design 

errors and (2) the ability of the fieldbus to guarantee deterministic responses. The IEC 61784 

standards (IEC 61784-1TPD

29DPT and IEC 61784-3TPD30DPT) address extensions to the fieldbus technology 

described in IEC 61158 to render the technology compatible with IEC 61508. Gen III and III+ NPPs 

currently undergoing certification [e.g., the European Pressurized Reactor (EPR)] will use fieldbus 

technology, such as PROFIBUS to communicate between safety and nonsafety systems. The 

PROFIBUS has some attractive features with regard to NPP application. These include (1) a 

master/slave messaging model that results in a deterministic communication protocol and 

(2) suitability for use in redundant architectures. 

3.2 DETAILS OF TECHNOLOGY/INDUSTRY TRENDS 

3.2.1 Wired Instrument Networks 

The IEC 61784 standards (IEC 61784-1X

29X and IEC 61784-3X30X) address extensions to fieldbus 

technologies described in IEC 61158 in a way compatible with IEC 61508. These extensions are a 

standardized means of supporting real-time, safety-related and security-related applications. 

IEC 61784 lists specifications for seven fieldbus technologies (protocols): 

• FOUNDATION Fieldbus (FF), 

• ControlNet, 

• PROFIBUS, 
12 

• P-NET, 

• WorldFIP, 

• INTERBUS, and 

• SwiftNet. 

3.2.1.1 Foundation Fieldbus 

Foundation Fieldbus (FF), designated as Communication Profile Family 1 in IEC 61784-3,X

30X is an 

open architecture that supports all-digital, serial, two-way communication systemsTPD

31DPT. Two levels of 

physical abstraction for communication are used: H1 and high-speed Ethernet (HSE, 100 Mbit/s). The 

H1 layer (31.25 kbit/s) interconnects field equipment such as sensors, actuators, and input/output 

(I/O). The H1 physical layer receives messages from the H1 communication stack and converts them 

into physical signals on the FF transmission medium and vice versa. The HSE layer provides 

integration of high-speed controllers such as programmable logic controllers (PLCs); H1 subsystems–

via a linking device; data servers; and workstation. A simplified network layout is shown in XFigure 5. X 

Figure 5. FOUNDATION fieldbus network.P

26P

The H1 layer uses the Manchester Biphase-L encoded current modulation at 31.25 kHz. The signal is 

called “synchronous serial” because the timing information is embedded in the data stream. On the 

H1 physical layer, up to 32 devices can be supported at 31.25 kbit/s on a 1900-m cable with a 

maximum spur length of 120 m. The number of devices possible on a fieldbus link depends on factors 

such as the power consumption of each device, the type of cable used, number of repeaters, etc. On 

the H1 communication stack, two types of devices can be defined in the DLL specification: basic 

device and link master. Link master devices are capable of becoming the link active scheduler (LAS). 

The LAS has a list of transmit times for all data buffers in all devices that need to be cyclically 

transmitted. 

The FF safety communication layer specified in IEC 61784-3-1TPD

32DPT makes it possible to use intelligent 

devices in a safety-related system adding more capability. Moreover, the system can meet its specific 

safety-integrity-level requirements. 
13 

3.2.1.2 PROFIBUS 

Defined as Communication Profile Family 3 by IEC 61784-3, PROFIBUS is based on the cyclic data 

exchange of a bus controller with its associated field devices using a one-to-one communication 

relationship. Any mix of standard and safety-related devices can be connected to a network assigned 

to a single controller. The protocol also allows assigning safety tasks and standard tasks to different 

controllers. Acyclic communications between devices and controllers or supervisors such as 

programming devices are possible for configuration, parameterization, diagnosis, and maintenance 

purposes. 

The functional safety is realized by four measures: (1) consecutive (virtual) numbering, (2) watchdog 

time monitoring with acknowledgement, (3) codename per communication relationship, and 

(4) cyclic redundancy checking (CRC) for data integrity. Each safety device sends an 

acknowledgement message with a safety protocol data unit PDU. A separate watchdog timer on both 

the sender and the receiver side is used for each one-to-one communication. A unique “codename per 

communication relationship” is established for authentication reasons. The codename is encoded 

within an initial CRC signature value, which is recalculated every n hours. 

There are different application-oriented emphases that are not specifically defined but have found 

wide acceptance. Each main emphasis is built from a typical combination of modular elements as 

depicted in XFigure 6X. PROFIBUS DP (Decentralized Periphery) is the main emphasis for factory 

automation based on RS485 transmission technology. PROFIBUS PA (Process Automation) is 

mainly used for process automation, usually with Manchester Coding Bus Powered-Intrinsic Safety 

(MBP-IS) transmission technology. Motion control with PROFIBUS is the main emphasis for drive 

technology using RS485 transmission technology. The application profile for motion control is 

known as PROFIdrive. PROFIsafe is the main emphasis for safety-related applications based on 

either RS485 or MBP-IS transmission technology. 

Figure 6. Application-oriented features of PROFIBUS. 

At the protocol level, PROFIBUS DP is offered in three versions: DP-V0, DP-V1, and DP-V2. 

DP-V0 provides the basic functionality of DP such as cyclic data exchange, station and module 

diagnosis, and channel-specific diagnosis. DP-V1 introduces certain enhancements to DP-V0 with 

extensions such as acyclic data communication and alarm definitions. DP-V2 contains additional 

functionalities toward drive technology with extensions such as isochronous slave mode and slave-toslave communication (known as DXB or data exchange broadcast). These DP versions are 

extensively specified by IEC 61158. 

Application 

Profiles, e.g.

Ident Systems 

DP-Stack 

(DP-V0—V2) 

RS485 

PROFIBUS DP 

(Manufacturing) 

Application 

Profiles, e.g. 

PA Devices 

DP-Stack 

(DP-V1) 

MBP-IS 

PROFICUS PA 

(Process) 

Application 

Profiles, e.g.

PROFIdrive 

DP-Stack 

(DP-V2) 

RS485 

Motion Control 

with PROFIBUS

Application 

Profiles, e.g.

PROFIsafe 

DP-Stack 

(DP-V0—V2) 

RS485 

MBP-IS 

PROFIsafe 

(Universal) 
14 

Safety implementations are specifically presented in IEC 61784-3 for several fieldbus technologies, in 

conformance with higher-level IEC standards such as 61500, 61508, and 61511. A major component 

of the safety concept is the safety communication layer (SCL), a communication layer in the sense of 

the open system interconnects model, as illustrated in XFigure 7X. This safety feature is incorporated 

into safety-related equipment, represented as a safety node, so that safety messages passed between 

any two nodes are processed at the sending and receiving end nodes. The SCL’s main function is to 

ensure that the system, as a whole, maintains the integrity of the safety-related functionality 

regardless of any communications errors that might occur. It covers possible transmission faults, 

remedial measures, and considerations affecting data integrity. For example, a safety layer can 

implement an additional CRC function to reduce the probability of accepting a corrupted message to 

the level required for a given safety function. The IEC specifications list the type of communications 

errors and the safety measures that effectively mitigate them. 

Safety

Communication

Layer

Application

Layer (optional)

Data Link Layer

Physical Layer

Safety

Communication

Layer

Application

Layer (optional)

Data Link Layer

Physical Layer

Gateway

Application

Layer (optional)

Data Link Layer

Physical Layer

FAL

DLL

PhL

Internal Bus

Communication

Network

Repeater

Different

Protocols

Figure 7. Three-level layer model with safety communication layer applied 

to a safety system network. 

An interesting concept in the standard is the use of “black channel,” an approach in which a safety 

functionality, represented by PROFIsafe protocol in compliance with IEC safety standard 61508, 

resides on top of the existing protocol, represented by the standard PROFIBUS protocol. The black 

channel concept provides improvement in the reliability of the overall communications system. Its 

use in a safety-related communications channel is justified by adding the SCL prescribed by the 

standard. The SCL is present at both black channel endpoints as shown in XFigure 8X. The SCL 

performs safety-related transmission functions and checks on the communication to ensure that the 

integrity of the link meets its requirement. Upon detecting a problem, the SCL will attempt to make a 

correction, but if it fails, it will place the system in a safe state (e.g., by tripping the reactor). The IEC 

standard can provide information regarding the possible communication errors and the means of 

detecting and preventing these errors. The standard, however, cannot prescribe a universal method for 

taking the system to a safe state in the event of an error. 

Figure 8. Illustration of black channel implementation. 
15 

3.2.2 Wireless Communications 

There are several trends in wireless communications, ranging from high-bandwidth communication 

links to radio-frequency identification (RFID), that have the potential to improve the communication 

performance in NPPs, but wireless communications could also introduce security and possible safety 

challenges.The three primary concerns when considering wireless communications are security, 

reliability, and spectrum management. Wireless technologies and related issues are examined in this 

section. 

For several years,truly broadband wide-area communications were developed and implemented using 

fiber-optic cables.However, the new trend is to provide communication backbones using wireless 

links with some type of infrastructure such as wireless networking nodes piggy-backing on cell-phone 

towers, microwave links, or a combination of the two. The IEEE 802 family of standards has been 

developed for wireless communications in conjunction with various networking platforms. Four basic 

networking platforms; personal area network (PAN), local area network (LAN), metropolitan area 

network (MAN) and wide area network (WAN) have been reviewed, with emphasis on wireless 

connectivity of devices to these networks, as shown in XFigure 9X. 

PAN

LAN

MAN

WAN

< 10m

< 100m

< 5 km

< 15km

1- 600 Mb/s

WiFi- 802.11a/b/g/n

WiMax – 802.16a/e

MobileFi – 802.20

1 Mb/s

70 Mb/s

1 Mb/s

Bluetooth – 802.15.1

Zigbee – 802.15.4 250 kb/s

WiMedia – 802.15.3

100- 500 Mb/s

Figure 9. TWireless protocol coverage.T 

The PAN standard, which is governed by IEEE 802.15,TPD

33DPT is designed to provide a point-to-point 

wireless connectivity between devices equipped with the same wireless protocol (Bluetooth, ZigBee, 

or Wi-Media). It is limited in its coverage to the immediate space surrounding a device (e.g., a single 

room) with a range on the order of 10 m. The bit transfer rate varies from 250 kbit/s to 500 Mbit/s 

depending on the type of protocol used in conjunction with the communicating devices. 

The LAN standardized by IEEE 802.11TPD

34DPT is a network design for larger area coverage (on the order of 

100 m). Most LANs are confined to single building or group of buildings. In addition, one LAN can 

be connected to other LANs to provide much wider coverage using telephone lines as well as wireless 

transmission. Wireless communication over LANs is accomplished using the wireless fidelity (Wi-Fi) 

protocol. With this protocol, data can be transmitted at relatively fast rates, varying between 1 to 

600 Mbit/s, depending on the IEEE standard being adopted (802.11a, 802.11b, 802.11g, 802.11n) by 
16 

the network and the communicating devices. The higher data rate is attributed to version 802.11n as a 

result of using multi-input, multi-output (MIMO) and orthogonal frequency division multiplexing 

(OFDM) techniques. 

MANs can deliver point-to-multipoint communication among devices within a business building or 

an entire block of business buildings. MAN transmissions can cover a geographic area larger than that 

covered by an even larger LAN. Such networks are typically found in urban areas where large 

obstructions typically exist. They are capable of covering areas in the range of 5 km and can even 

extend to wider areas with the use of repeaters. The wireless communication protocol used in 

conjunction with MANs is the Wi-Max (worldwide interoperability for microwave access), which is 

based on the IEEE 802.16 standardTPD

35DPT and is capable of transmitting data at 70 Mbit/s. Worldwide 

interoperability is even made possible by merging technologies from different networking platforms. 

WANs are the result of such mergers allowing coverage worldwide by interconnecting LANs and 

MANs through routers, repeaters, and even satellites to form even wider geographical areas—in the 

range of 15 km. Wireless connectivity to WANs is achieved using the Mobil-Fi protocol, which is 

based on the IEEE 802.20 standard.TPD

36DPT This wireless technology extends high-speed wireless access to 

mobile users with a relatively fast data rate of 1 Mbit/s. 

Technical overviews of the wireless technologies used in conjunction with the four network platforms 

are presented in the following five subsections. 

3.2.2.1 Wireless Fidelity 

Wireless Fidelity (Wi-Fi) is a wireless technology most widely used in routers to provide Internet 

network connectivity for devices such as computers. Other applications include network connectivity 

for consumer electronics such as television, DVD players, and digital cameras. Wi-Fi products are 

commercially available in four different formats: 802.11a, 802.11b, 802.11g, and 802.11n, with data 

rates between 1 and 600 Mbit/s. Data can be transmitted between devices supporting this technology 

within the 100 m range at a rate ranging from 1 to 600 Mbit/s, depending on the IEEE standard being 

used. Current trends indicate that two of the standards, 802.11a and 802.11b, are being phased out and 

are being replaced by 802.11g, which combines the attractive features from both standards (speed 

from 802.11a and broad compatibility of 802.11b). 

The higher data rate (600 Mbit/s) is attributed to the latest version, 802.11n, as a result of using 

MIMO and OFDM techniques. The main purpose for developing Wi-Fi technology was to provide 

wireless access to the Internet using high-speed data transmission, with no emphasis on low power 

consumption; therefore it is not deemed applicable to sensors and actuators. 

Another advantage of Wi-Fi is that it operates in the 5-GHz unlicensed national information 

infrastructure (UNII) band. This is particularly desirable because the 2.4-GHz industrial, scientific, 

and medical bands have become overcrowded with ZigBee, 802.11b and 802.11g, Bluetooth, and 

even microwave ovens. 

State-of-the-art wireless technologies make it possible to interconnect devices with different wireless 

protocols such as connecting personal digital assistants with computers, thus merging PAN with 

LAN. This would allow wireless accessibility within industrial plants for accessing/sharing files that 

assist plant operators in performing various tasks. 
17 

3.2.2.2 ZigBee 

ZigBee is a wireless technology based on the IEEE 802.15.4 standard and developed for low-power, 

low-data-rate communications of 250 kbit/s with area coverage of 10 to 70 m. ZigBee-enabled 

devices can typically be found in the personal market sector (e.g., home automation), business sector 

(e.g., commercial office applications), and industrial sector (e.g., sensors for monitoring temperature, 

radiation, and pressure). Sensors with ZigBee interface can be potentially applied to monitor the 

health of NPPs. As an example, temperature transducers and level sensors can be placed within a 

coolant chamber to monitor and report the coolant operating conditions (e.g., temperature, level). 

These types of monitoring applications could be extended to radiation sensors and other types of 

warning sensors placed throughout a plant to warn against airborne releases of radionuclide and 

abnormal radiation levels in the work place. 

Another advantage of ZigBee products is the ability to maintain power consumption at a minimum by 

entering a sleep mode when the device is not active. In sleep mode, the device reduces its power 

consumption to a minimum, and it can be awakened at any time. There is typically a 15 ms delay for 

a device to “awaken” from sleep mode, and it would take another 15 ms delay for the active slave to 

access the channel. Wireless sensors (ZigBee devices) could also serve to aid the functionality of 

various security devices. Whether used with motion sensors on the ceiling or pressure sensors within 

the floor, they could be used to monitor restricted areas for unauthorized accessed and alert a central 

security system, which in turn could initiate security measures (e.g., controls for lights, alarms, door 

locks, and cameras). 

One of the limiting factors for Zigbee is the transmission coverage, which is limited to 10 m. This 

limitation can be overcome by relaying information between several devices to extend the coverage 

even further. ZigBee can conform to various network topologies such as the star and peer-to-peer. 

3.2.2.3 Bluetooth 

Bluetooth is a radio standard and communications technology based on the IEEE 802.15.1 standard. It 

was developed as a wireless cable-replacement device used mainly in conjunction with computers but 

also now finding applications in cell phones. It was developed primarily as a low-power, lower cost 

alternative to Wi-Fi. Bluetooth technology is implemented in a low-cost chip that can be plugged into 

any device capable of supporting wireless communications and transmitting data at a rate of 1 Mbit/s. 

The coverage, however, can range from a few meters to a hundred meters, depending on the 

transmitting power level (Class 1: power—100 mW (20 dBm), range—~100 m; Class 2: power—

2.5 mW (4 dBm), range—~10 m; Class 3: power—1 mW (0 dBm), range—~1 m). A typical 

application for a Bluetooth-compliant device is communication with computers. Such capability 

allows Bluetooth to be used in a wide range of potential applications because computers are 

extensively used in practically all facets of research and in industrial processes for monitoring and 

control purposes. However, the application of Bluetooth technology in industrial settings is still 

limited to performing administrative tasks rather than playing a key role in establishing digital 

communication networks for use in I&C applications. 

3.2.2.4 Ultra-Wideband 

The ultra-wideband (UWB) is an emerging short-range radio technology that complements longer 

range radio technologies such as Wi-Max and Wi-Fi. It is intended for low-power radio transmission 

in compliance with the IEEE 802.15.3a standard (i.e., capable of relaying data from a host device to 

other devices in an area within 10 m). The UWB can operate in the frequency range of 3.1 to 

10.6 GHz without licensing requirement and transmits information by spreading it over a bandwidth 
18 

exceeding 500 MHz. Data transmission is accomplished by generating radio energy at specific time 

instants and occupying large bandwidths, which can be considered as a pulse-position or timemodulation technique. According to the Federal Communications Commission ruling, the bandwidth 

can be the lesser of 500 MHz or 20% of the center frequency. One of the main advantages of the 

UWB transmitting signal is that it is less likely to cause interference with the conventional narrow 

band radio signals due to its high bandwidth and short-range coverage. Early UWB systems were 

developed for the military as surveillance tools (radar imaging, precision positioning and tracking) 

because of their ability to transmit through trees and ground surfaces. More recently, the UWB 

technology has begun to focus on consumer electronics (audio and video applications). 

Several versions of the UWB platform are being developed for different applications. Wi-Media 

UWB is one protocol that is considered the basis for the industry’s first UWB standards. It is 

designed as a common radio platform incorporating a medium access control layer and physical layer 

specifications based on multiband OFDM. This development enables short-range multimedia file 

transfers at data rates of 480 Mbit/s with low power consumption. The Wi-Media UWB has been 

specifically aimed at markets such as the PC, consumer electronics, mobile device, and automotive 

markets and complementary WPAN technologies such as Bluetooth and the Certified Wireless USB. 

3.2.2.5 Worldwide Interoperability for Microwave Access 

Worldwide interoperability for microwave access (Wi-Max) is a telecommunication technology 

conforming to the IEEE 802.16 standard and described as a standards-based technology enabling the 

delivery of wireless broadband access as an alternative to cable and digital subscriber line. 

Wi-Max is aimed at providing broadband access to Internet services throughout the world. The 

protocol is very similar to the HiperMAN standard being used in Europe. Wi-Max technology has the 

potential for replacing the fiber optic and copper wire backbones of existing networks. Although there 

may be reluctance in urban environments to switch to wireless infrastructure, where existing wired 

infrastructure is already available, there is a need for this service within developing countries and 

rural areas where the resources are not available due to a limited customer base. However, because of 

the wide coverage range of Wi-Max, extending to 50 km, by using a minimum number of base 

stations, coverage can be provided to such remote places for a cost much less than installing a copper 

or fiber optic infrastructure. 

The wide coverage capability of Wi-Max is attributed to high transmitter power and the use of 

directional antennas. By limiting the maximum number of customers to 500 per base station, Wi-Max 

made it possible to increase the bandwidth provided to each customer. As a result, an overall high 

data rate could be achieved. Currently, Wi-Max is used in a strictly stationary service providing 

environment, where the receiving antenna is placed in a fixed location. To achieve wide coverage, the 

antennas are normally placed on rooftops, although development is underway to extend coverage to 

indoor environments. The fact that both the Wi-Max and Wi-Fi provides accessibility to wireless 

connectivity and the Internet, Wi-Max- and Wi-Fi-enabled devices can coexist within the same 

wireless networking infrastructure. In such a case, the Wi-Max is used to transmit data over larger 

distances (kilometers) to a network infrastructure such as the MAN, and Wi-Fi would provide data 

access through the Internet within a limited region (meters). 

Similar to both Wi-Media and portions of Wi-Fi, Wi-Max also incorporates an OFDM system for 

modulation. This system can operate within two frequency ranges, either the 10 to 66 GHz range or 

the 2 to 11 GHz range. In the higher frequency range, a line-of-sight (LOS) path is required due to the 

inability of high-frequency signals to propagate through walls. In contrast, low-frequency signals do 

not require LOS. The addition of the lower frequency range is part of the 802.16a section created for 
19 

the standard. Because there is a large amount of bandwidth available to Wi-Max, it is able to achieve 

a higher data rate than Wi-Fi. In a single channel, these data rates can reach 75 Mbit/s, with a 

possibility of 350 Mbit/s using multiple channels. The ability to use multiple channels allows 

Wi-Max to be expandable whenever more bandwidth is needed by just adding more channels. 

3.2.2.6 Radio-Frequency Identification 

Radio-frequency identification (RFID) is an automatic identification and data capturing technology 

that is complementary to bar coding.An RFID system consists of a tag, antenna, and transceiver.The 

tag is an IC containing the RF circuitry and information to be transmitted.The antenna and the 

transceiver are used to pick up the RF signals transmitted by the tag and transfer the information to a 

processing device, typically a computer.One of the key differences between the RFID and bar code 

technology is that the RFID eliminates the need for the (LOS transmission required by the bar code 

technology). RFID tags are generally one of two types, passive or active.Active tags require an 

internal power source to power the transceiver; the power supply also powers the tag’s controller. 

Passive tags do not contain an internal power source. Consequently, a passive tag requires power 

from a transmitter, which also sends the query to the tag. There are many RFID products on the 

market, but tag compatibilty for a particular application is still a major issue. 

Some government agencies have begun introducing RFID technologies into their facilities for asset 

and personnel accountability. At present, the main benefits are for property accountability (i.e., the 

prevention of loss and theft) and for personnel accountability (e.g., ensuring that all personnel have 

cleared the building during an evacuation). Hence, RFID can save significant costs and improve the 

safety of the workforce. 

The main concerns for applying RFID technology focus on security issues, which include the 

following. 

1. Data collected by the RFID system should have a one-way portal into the facility’s intranet. 

2. Depending on job classification, some people or assets and their whereabouts may need to be 

treated as sensitive information and require classification controls. 

3. Personnel tags should not be allowed to leave the facility area or be used by the same person 

every day to prevent outsiders from tracking individuals. 

4. Asset tracking should include only a generic property number, not model numbers, serial 

numbers, or other descriptive text. 

5. Adequate physical separation will be required between the boundary of a controlled facility, 

where the tags are used, and uncontrolled areas where unauthorized access of data can be 

accomplished by intercepting the RF transmitted signals. 

3.2.2.7 Wireless Communications in the Power/Nuclear Industry 

Wireless communication technologies are widely applied in the nonnuclear industry to improve 

in-plant communications, reduce operating costs, and reduce human error. The challenges that impede 

complete acceptance of wireless technology in the nuclear environment remain (1) how to ensure 

complete independence between systems (e.g., between safety and nonsafety), (2) how to ensure 

reliable performance in noisy (e.g., high electromagnetic/radio-frequency interference) environments, 

and (3) cyber security. It is likely that the ever increasing improvements in wireless technology will 

result in improved reliability and increased data security, which in turn could result in greater 

acceptance of wireless technologies within the NPP industry. 
20 

Applications of wireless communications in power generation facilities in general include voice and 

data communications to employees and field crews, distributed supervisory control and data 

acquisition to substations and power line devices, wireless LAN devices for office uses, automated 

intelligent metering, geographical-information-system- (GIS-) based work management, alarm 

systems, and emissions monitoring. Wireless technology has already been used in applications in a 

few NPPs. An example is Exelon Nuclear’s Limerick Generating Station in Montgomery County, 

Pennsylvania, where vibration and temperature sensors equipped with RF transmitters are used to 

monitor the fans that are used to exhaust turbine enclosures. Another plant that adopted wireless 

technology is San Onofre’s NPP in California. In this plant, wireless temperature sensors and 

transmitters have been installed to remotely monitor several 2,550 hp plant motors.TPD

37DPT 

As mentioned previously, the nonnuclear power industries have been experiencing increasing 

application of wireless technologies. Many existing wireless systems have been modified specifically 

for use in the power generating industries. Power companies like TXU Energy in Texas,TPD

38DPT for 

example, have improved their plant communications systems by installing fiber-optics-based LANs 

as backbone systems for supporting existing wired and planned wireless systems. Wireless access 

points have been deployed throughout the plant to support multimedia applications. Voice-overInternet protocol technology is being used to accommodate mission critical and routine voice 

communications. Applications of wireless systems include two-way radioing, basic telephony, online 

equipment monitoring, connectivity to intranets and the Internet, and remote video monitoring. 

Reliability is ensured through network redundancy and backup power sources. 

Ontario Power GenerationTPD

39DPT is an example in which a different approach has been adopted for 

integrating several existing communication systems, including a 400-MHz radio system, Nortel 

companion phone system, in-house 400-MHz voice pagers, commercial cellular and paging systems, 

and emergency communication radios, into a more modern infrastructure meeting current 

requirements. A virtual private network (VPN) based on a commercial cellular system has been 

selected based on their needs and available communication equipment, among other options, for this 

task. The objectives of the VPN are (1) to support station containment outage (SCO); (2) to comply 

with the communications industry; and (3) to meet NPP security’s mandate to provide contiguous and 

seamless communications on site and within the powerhouse, between sites, and with regional police 

communication centers. 

RLW Inc.TPD

40DPT has built a wireless platform for deployments in industrial environments like NPPs. This 

is a stand-alone platform containing many components of communication equipment such as data 

collection devices; sensors; a LAN; cameras; and handhelds/notebooks, for plant monitoring and 

control purposes. 

3.2.2.8 Quantifying the Reliability of Wireless Communications 

The reliability of a communication system is measured by its bit error rate (BER) or packet error rate 

(PER). This is a measure of the average ratio of the bits in error to the total transmitted bits. It is 

useful to measure the BER of the communication medium over the entire range of conditions in 

which it is intended to operate. Unacceptable BER results in unacceptable communications. 

Generally, BER values higher than 10P

–3P

 are not acceptable for any application. However, some BER 

requirements are application-specific and more stringent: the BER value for video applications, for 

instance, must be less than 10P

–5P

.There is a one-to-one relation between the received power/signal-tonoise-ratio (SNR) and the BER. In addition, the SNR requirement for a particular BER is also 

application specific. For an additive white Gaussian noise (AWGN) channel, if the SNR requirement 

for a certain BER value increases above 15 dB, it is considered unacceptable. For a fading channel, 

on the other hand, this value can be as high as 30 dB. 
21 

The first step in acquiring the desired BER is to carefully select the modulation schemes in the 

physical layer and is generally followed by a forward error-correction coding (FEC). The FEC detects 

and corrects the bits in error after the demodulation. The tradeoff of the FEC is the available 

bandwidth and decoding complexity versus the BER improvement. Retransmission of the entire 

packet can be used to improve the PER. Combinations of modulation; FEC, diversities spreading, and 

interference cancellation are used to achieve the desired BER. Parameters to be considered are 

(1) required transmitted power, (2) available bandwidth, and (3) receiver complexity. To protect 

against tampering with the data, a cryptographically -derived media access code address may be used. 

The encryption process consists of a hashing algorithm such as SHA-1 or MD5 combined with an 

operation involving a secret key. Cryptographic hash functions provide transformation of an input to a 

fixed-sized string, also referred to as the hash value, digital fingerprint, digest, or a checksum. MD5 

and SHA-1 are the two most commonly used hash functions. 

3.2.2.9 Protecting Wireless Communications against Unauthorized Access 

The most commonly used method to protect against unauthorized access is encryption. If a 

commercial-grade encryption is used, such as 128-bit secret key encryption, 1500-bit public key 

encryption, or U.S. Government Type 1 encryption, the data can then be considered protected against 

unauthorized access. Such protection depends greatly upon the protection afforded the keys. 

The next most commonly used method of protecting data against tampering is physical protection. 

Proper shielding can be an effective means for preventing unauthorized access to the RF signals 

transmitted by sensors. If the strength of the transmitter and the perimeter distances are such that the 

signal strength outside the perimeter is sufficiently low, it should also be quite difficult for an 

adversary to intercept the signals. 

Another method that can be used is directional transmission. Transmitting data directly toward the 

intended receiver reduces the locations from which the transmissions may be received. If this method 

is combined with low power signals, it can be even more effective. A further optimization of this 

technique could involve multiple access points using phased array antennas. The signal can be 

multiplexed between the access points so that parts of the signal are transmitted from each access 

point directly toward the receiver. With this method, an unauthorized person would not be able to 

intercept the entire signal without having at least one antenna located in line with each transmitter and 

the receiver. 

3.3 REGULATORY IMPACT OF COMMUNICATIONS AND NETWORKING 

With regard to digital communication (whether wired or wireless), the overriding regulatory issue is 

maintaining not only physical and electrical independence but also data independence between safety 

and nonsafety systems. 10 CFR 50.55a(h), “Protection and Safety Systems,” requires compliance 

with IEEE Standard 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power 

Generating Stations.” Clause 5.6 of IEEE Standard 603-1991 requires redundant safety systems to be 

independent of one another. IEEE 7-4.3.2-2003 addresses communication independence. In general, 

however, current industry guidance documents such as IEEE Standards 603 and 7-4.3.2 do not 

sufficiently define a level of detail for evaluating interdivisional communications independence. 

Indeed, some provisions of IEEE Standard 7-4.3.2 have been found not to be suitable for endorsement 

by NRC. In Regulatory Guide 1.152, Rev. 2,TPD

41DPT IEEE Std. 7-4.3.2-2003 is presented as a method 

acceptable for satisfying NRC’s regulations with the exception of five informative annexes, Annexes 

B–F. (IEEE Std. 7-4.3.2 is also referenced by other NRC documents such as Regulatory Guide 

1.206,TPD

42DPT Regulatory Guide 1.209,TPD43DPT and NUREG-0800, “Standard Review Plan”TPD44DPT). In addition, IEEE 

7-4.3.2 is currently undergoing revision, and at this point, it is not known whether the revision will be 
22 

suitable for endorsement or consistent with current NRC positions.TPD

45DPT Therefore there is the need to 

establish acceptance and review criteria for safety systems communications that can be uniformly 

applied to a variety of digital safety system designs. To address these concerns, NRC issued the 

Interim Staff Guidance DI&C-ISG-04, “Highly-Integrated Control Rooms—Communications Issues 

(HICRc),” in September 2007.X

45X In addition, Kisner et al. have documented in a draft NUREG/CRTPD46DPT a 

technical basis for guidance that specifically addresses issues related to communication among safety 

divisions and between safety-related equipment and equipment that is not safety related. The report 

examines (1) accepted networking consensus practices adopted by various standards organizations in 

the United States and internationally, (2) operating experience of international power reactors using 

digital network communications in safety systems, and (3) failure mechanisms arising from several 

possible network architectures and message types. The NUREG/CR uses these studies as a basis to 

develop a structured approach to provide review guidance for the evaluation of safety-to-safety and 

non-safety-to-safety communications systems. 

The independence issue with regard to wireless communications systems in NPPs is not so easily 

resolved. Howlader, Korsah, and EwingTPD

47DPT have developed the technical basis for regulatory guidance 

on implementing wireless communications in NPPs. Wireless systems are likely to be limited in the 

foreseeable future to non-safety-related diagnostics and maintenance systems such as the ones already 

discussed, inventory management systems, and voice and data communications to employees and 

field crews. 
23 

4. MICROPROCESSORS AND OTHER INTEGRATED CIRCUITS 

4.1 MICROPROCESSORS AND OTHER INTEGRATED CIRCUITS OVERVIEW 

The evolution of semiconductor devices has moved from the single transistor (discrete design) to ICs 

with various complexities, to powerful microprocessors with various capabilities, to more advanced 

integrated circuits designed for specific applications [application-specific integrated circuits—

(ASICs)]. The direction of research and development (R&D) in the semiconductor industry is 

exemplified by the development by Intel in early 2007, following years in research, of a prototype 

microprocessor called Penryn with two versions: dual-core microprocessor with 410 million 

transistors and quad-core with 820 million transistors.TPD

48DPT These processors were developed with 45 nm 

complementary metal-oxide semiconductor (CMOS) technology using high-k plus metal gate 

materials. In addition, Intel is in the process of launching an R&D program to develop 32 nm 

technology for future chips. The successful development of the high-k (replacing the SiOB

2B insulation, 

which was used up to the 65 nm generation presently used by many semiconductor manufacturers), in 

conjunction with the metal gate (replacing the silicon gate electrode used up to the 65 nm generation) 

made it possible to shrink the insulation layer between the gate electrode and the transistor channel in 

size but yet provide enough isolation needed to prevent current leakage in the off-state while at the 

same time allow high conduction current in the on-state. 

The performance level of field programmable gate arrays (FPGAs) and their associated software tools 

have advanced such that they are now being considered in the design of complex digital control 

systems. FPGAs can typically include as many as 8 million gates and can incorporate multiple 

implementations of complete microprocessors on a single chip. Software tools are available to 

compile a wide variety of programming tools, used to describe the FPGA design, into FPGA 

configuration code. There are several programmable tools that are commercially available such as the 

Very High Integration Hardware Description Language (VHDL) code, AND/OR gate level hardware 

schematics, MATLAB m-code programs, MATLAB Simulink diagrams, and C programs. 

For digital safety systems, one concern has been the need to ensure near-error-free performance. 

However, the growing system complexity and shrinking feature size of semiconductor devices 

introduce new reliability concerns and the potential for new aging phenomena, thus making it even 

more difficult to guarantee delivering future products free of errors. 

4.2 TECHNOLOGY TRENDS 

4.2.1 Josephson Junctions 

A Josephson junctionTPD

49DPT is an electronic circuit composed of two superconductors separated by a thin 

insulating oxide layer (typically only 10–20 Å thick), resulting in tunneling of Cooper pairsTPD

50DPT of 

electrons through the junction. Cooper pairs are electron pairs that form when a substance is cooled to 

the point where it becomes superconductive (usually close to absolute zero). The Cooper pairs on 

each side of the junction form a wavefunction. In the dc Josephson effect, a current proportional to 

the phase difference of the wavefunctions can flow in the junction in the absence of a voltage. In the 

ac Josephson effect, the junction will oscillate with a characteristic frequency, which is proportional 

to the voltage across it. Due to the fact that frequencies can be measured with high accuracy, a 

Josephson-based device offers the accuracy that qualifies it as a voltage standard. 

A device operating on the principle of the Josephson effect is capable of operating at very high speeds 

when operated at near-absolute-zero temperatures. Josephson junction logic gatesTPD

51DPT,

TD

52DTP

 have been 

available for some time, but have been considered impractical because they require cryogenic 
24 

cooling. They are the fastest logic available, with clock speeds up to 750 GHz. Recently HYPRES, 

Inc. (HTwww.hypres.comTH) has applied this technology to high-speed analog-to-digital converters 

(ADCs) for use in software defined radio (SDR) applications. They have built SDR systems for the 

U.S. Navy that have 24-bit resolution at 2 GHz and can operate at speeds up to 20 GHz. HYPRES is 

also developing a lighter weight cooling system, cryocoolers, based on closed-cycle Stirling engines 

to cool the electronics instead of liquid helium. 

Although Josephson junctions are not likely to be used directly in safety-related systems, the 

technology can be used to build very precise instrumentation. This instrumentation can potentially be 

used to measure RF and microwave propagation characterization of nuclear facilities, radiation 

analysis, and general signal processing. 

4.2.2 Multicore Processors 

Multicore processors are microprocessors that contain more than one central processing unit or core. 

This arrangement allows parallel processing, where separate programs run on each processor core and 

data are exchanged between processors as needed. Locating multiple cores on one chip enables 

enhanced communication between the cores and provides higher performance (e.g., higher data 

transfer) than microprocessors in separate packages. Parallel processing has power dissipation 

advantages because doubling the number of processors only doubles power consumption, whereas 

doubling the clock speed can increase the power consumption by as much as six-fold.X

53X

 Another 

advantage of multicore processing is that context switching is reduced, resulting in improvements in 

interrupt processing and real-time control. 

Multicore processors with four cores, also called quad cores, from IntelTPF

*

FPT and AMDTPF

†

F are now available PT

for use in desktop computers. A more radical design called the Cell Broadband Engine (Cell/BE) is 

available from IBMTPF

‡

FPT that has a Power Architecture core with eight specialized coprocessors called 

synergistic processing elements (SPEs) in addition to a 64-bit power processing element (PPE) acting 

in a supervisory capacity. Present BE performance can be as high as 204.8 GFLOPS per second. 

Operating system support for multicore processors is now available for Windows and Linux. Mercury 

Computer SystemsTPF

§

FPT offers a development tool, the Mercury MultiCore Framework, for programming 

the Cell/BE-based processor. 

Multiprocessor systems on a chip (MPSoC) components are derived from multicore processors for 

embedded applications. MPSoC technologies are widely used in embedded processor applications 

such as digital signal processors, network processors, and graphics processor units. At present, there 

is no clear and crisp classification for multicore processors and MPSoCs. However, the performance 

and software programmability of both technologies are affected by four main issues.TPD

53DPT 

1. The type of processing elements used for performing the actual computation determines the 

choice of compilers; specific tools need to be customized to support a specific architecture. 

2. The communication within a chip and between chips determines how long processors have to 

wait before data can be accessed. 

3. The types of memory architectures used on and off chip have a profound impact on latencies in 

the processes accessing data. 

 

TP

*

PTHwww.intel.comTH TP

†

PTHwww.amd.comTH TP

‡

PTHwww.ibm.comTH TP

§

PTHwww.mc.comTH 
25 

4. Optimization of the hardware architecture for the applications running on them very much 

impacts whether the programming is straightforward (i.e., whether it is obvious which portions 

of a multicore system are running which tasks). 

4.2.3 Parallel Computer Architectures 

The deployment of sensors in conjunction with digital signal processing (DSP) algorithms to several 

of the emerging computational platforms (e.g., the Cell BE processor) will require selecting and 

implementing a parallel computing architecture framework. Because there are different architectures 

where each architecture is designed to optimize some specific parameters or functions, it would be 

important to understand the tradeoffs involved among the various architectures based on the intended 

application. One of the most fundamental choices is between the single-instruction, multiple-data 

(SIMD) operating architecture and the multiple-instruction, multiple-data (MIMD) operating 

architecture. In SIMD, a single instruction controls all SPEs while they perform different tasks. This 

is considered as the simpler paradigm. With MIMD machines, the processors operate concurrently 

and independently of each other and execute their own programs. This mode of operation offers more 

flexibility in the implementation process. Depending on the application requirements, SIMD 

machines may provide a comparable computing performance to the MIMD combined with the 

desirable features of having reduced size, weight, and power consumption. 

The second major design tradeoff is between shared and distributed local memory. With the shared 

memory setup, there is contention among the processors for access and only a small number of 

processors can be supported at any given time. With the distributed local memory, each processor has 

its own memory and data are passed as messages. However, this is an inefficient process as the time 

required to route messages between processors can be substantial. To overcome this challenge, one 

could adapt a real-time scheduler to quickly achieve near-optimum solutions on homogeneous 

concurrent processor ensembles. This can be accomplished by combining heuristic techniques for 

handling time complexity, with special instances of abstract data structures to handle space 

complexity. A real-time scheduling function can be incorporated to provide a nonpreemptive 

scheduling scheme. Once a task is assigned to a processor (a core in Cell semantics), it will be 

processed without interruption until the task execution is completed. In the event a processor is free, 

an instruction will be given for this processor to either start a new task or to idle until a new task can 

be assigned by the scheduler. 

4.2.4 Micro-Electromechanical Systems 

Micro-electromechanical systems (MEMS) is an enabling technology allowing integration of 

mechanical elements, sensors, actuators, and associated electronics on a common silicon substrate 

through microfabrication technology. The electronics for MEMS devices are fabricated using IC 

processes (e.g., CMOS, bipolar, or bipolar CMOS), while the micromechanical components are 

fabricated using compatible “micromachining” processes that selectively etch away parts of the 

silicon wafer or add new structural layers to form the mechanical and electromechanical devices. 

MEMS technology makes it possible to design and construct a complete system-on-a-chip. As a 

result, MEMS devices have many advantages, such as functionality, reliability, sophistication, and 

low cost, which are attributed to using batch fabrication techniques similar to those used for ICs. A 

class of microsensors has been developed for various physical measurements such as temperature and 

humidity, as well as measurements for harsh environments (chemical and biological). 
26 

SiTime, Inc.TPF

*

F has recently introduced a MEMS-based oscillato PT r that is commercially available. The 

oscillator was developed using a plate of silicon micromachined by MEMS techniques such that it is 

suspended over the silicon substrate. The suspension is configured to allow the plate to mechanically 

resonate and therefore eliminated the need for the bulky and more costly quartz crystal typically used 

in most commercially available oscillators. This oscillator is an advance over quartz oscillators 

because it is much smaller, more rugged, and has better aging characteristics. A MEMS oscillator can 

be fabricated in as small as 2.5 × 2.0 × 0.85 mm packages with an operating temperature rating of up 

to 125°C. In addition, the shock and vibration tolerance for this oscillator is enhanced over most 

oscillators using quartz crystal in their design. 

MEMs-based oscillators can be potentially used in digital I&C instrumentation design in NPPs 

because of the advantages they offer such as higher ruggedness, reliability, small footprint, and 

moderate cost. 

4.2.5 Dynamically Reconfigurable Integrated Circuits 

Reconfigurable computing combines some of the flexibility of software with the high performance of 

hardware by processing with devices such as FPGAs. Dynamically reconfigurable and selfconfiguring integrated circuits are the product of merging existing circuit technologies: the ASIC, 

digital signal processors (DSPs), system on a chip (SoC), and the FPGA. With this technology, a 

programmable device can be developed with computational capabilities enabling the device to 

self-configure and optimize and recover from faults and damage, as well as with reduction in size and 

power consumption and performance similar to an ASIC. 

Generally speaking, there are a limited number of options when it comes to executing 

computationally-intensive data processing applications. 

• ASICs: They offer high performance and low power consumption, but their functionality is 

hard-wired (i.e., they are not reconfigurable). They have long lead times, and they have high 

development costs. 

• FPGAs: They can be reprogrammed using hardware design methodologies, but they have 

relatively slow reconfiguration rates that make them unsuitable for applications requiring 

dynamic reconfigurability. Generally, they consume relatively large amounts of power compared 

to ASICs and SoCs. 

• DSPs: These special-purpose processors are highly programmable, but they consume a lot of 

power and are not capable of processing computation-intensive algorithms. 

• SoCs: Systems-on-a-chip devices combine ASIC hardware with DSP functions, hardware 

accelerators, blocks of memory, and peripherals. They share the pros and cons of ASICs and 

DSPs. 

A new family of devices based on the above technologies is called elemental computing arrays 

(ECAs), and it differs from the existing dynamically reconfigurable devices such as FPGAs in 

reconfiguration speed and reconfiguration flexibility; they can reconfigure either partially or 

completely in a single clock cycle. ECAs are made of functional blocks called “elements.” The 

elements are divided into three main classes: computation, storage, and signaling. The 

computation-class elements are as follows. 

 

TP

*

PTHwww.sitime.comTH, accessed 2008. 
27 

• BREO: UBUit UREU-UOUrderer. This enables shifting, interleaving, packing, and unpacking operations 

and can be used (un)packing, (de)interleaving, (de)puncturing, bit extraction, simple conditionals, 

etc. 

• BSHF: UBUarrel USHUiUFUter. This enables shifting operations and can be used for 16-bit barrel shift, 

left shift, right shift, logical shift, arithmetic shift, concatenation, etc. 

• MULT: 16 × 16 signed and unsigned UMULTUiplier with optional 32-bit accumulation stage; 

double 8 × 8 multiplies. 

• SALU: A USUuper arithmetic logic unit (UALUU) that performs 16-bit and 32-bit arithmetic and 

logical functions and can be used for sorts, compares, ANDs, Ors, XORs, ADDs, SUBs, ABS, 

masking, detecting, and leading 0’s. 

• TALU: A UTUriple UALUU that enables up to three simultaneous logical and arithmetic functions with 

conditional execution. This can be used for sorts, compares, ANDs, ORs, XORs, ADDs, SUBs, 

ABS, masking, detecting, Viterbi ACS, CORDIC, Motion Estimation, etc. 

Storage class elements are as follows. 

• MEMU: A UMEMUory U Unit providing random-access memory and sophisticated DAG (data 

address generation) capabilities used for data storage. 

Signaling class elements are as follows. 

• SME: A USUtate UMUachine UEUlement is used to implement sequential code, operate as a coprocessor 

with other elements, and operate as a virtual element for data-flow programs. The SME is a 

sequential processor, but—unlike traditional processors—it can be augmented by the other 

elements in the same cluster (we’ll talk about clusters in a moment). The SME is also used to 

implement the real-time operating system, run-time environment, housekeeping, test and 

resilience capabilities, and so forth. 

Elements are nonhomogeneous data-flow computational engines. All of the elements have the same 

form, but different capabilities, thereby allowing each type to be implemented in the most efficient 

manner. Because all of the elements have identical interfaces, this will facilitate adding new elements 

in the future, and also creating new devices with different mixtures of elements to target specific 

classes of problems. 

The next step up in the ECA hierarchy are so called “zones,” each of which comprises four elements 

that are directly connected to each other via a cross-point switch. The elements in a zone are tightly 

bound, communicating with each other in a single clock cycle. In turn, a cluster comprises four zones. 

The cluster is the smallest repeatable structure on an ECA device. All of the zones in a cluster 

communicate with each other by means of a number of special queues called “through queues.” Up to 

sixteen clusters can be grouped together to form a super cluster. Clusters within a super cluster can 

communicate resiliently through a hierarchical bus structure or more expediently through local 

interconnect. Similarly, up to 16 super clusters can be grouped together to form a matrix. Once again, 

super clusters within a matrix can communicate resiliently through a hierarchical bus structure or 

more expediently through local interconnect. This method of interconnecting levels of hierarchy can 

be extended indefinitely on a single chip, bounded only by the available levels of integration and 

device fabrication. Furthermore, ECA devices communicate via peripheral component interconnect-e 

(PCI-e) in the same hierarchical fashion, thereby extending the hierarchy to the board level. When it 

comes to running applications on an ECA, the computing fabric is extremely flexible, allowing the 
28 

various portions of a task to be distributed across computing elements for maximum speed and 

parallelism. Alternatively, a task with lower requirements can be “folded” onto a smaller number of 

elements (similar to the hardware design concept of “resource sharing”), thereby time-sharing the 

element with other portions of the same or other tasks. 

The hierarchical nature of the ECM fabric is critical for two reasons. First, it makes resource mapping 

and interconnection a tractable problem. A design that is organized hierarchically can be placed in 

any hierarchical region provided sufficient resources exist to accommodate it. Second, and of 

particular interest for mission-critical tasks, if some of the resources fail in a hierarchy, other 

hierarchical resources can be used instead. 

The nature of the ECA architecture resists any potential failure and, when a hard or soft failure does 

occur, it self-heals creating a fault-tolerant system. If one or more elements fail in a cluster, for 

example, that cluster’s SME can redirect tasks to other elements in the cluster or to other clusters. 

This form of reliability enables fully adaptive and extremely durable devices for use in safety-critical 

applications such as I&C in nuclear plants. 

4.2.6 Field Programmable Gate Arrays 

FPGA devices have been available for several years; however, the performance level of the devices 

and their associated software tools have recently advanced such that they are now being considered in 

the design of complex digital control systems. FPGAs can typically include as many as 8 million 

gates and can incorporate multiple implementations of complete microprocessors on a single chip. 

Software tools are available to compile a wide variety of programming tools, used to describe the 

FPGA design, into FPGA configuration code. Several programmable tools are commercially available 

such as the VHDL code, AND/OR gate level hardware schematics, MATLAB mcode programs, 

MATLAB Simulink diagrams, and C programs. 

A fundamental difference between FPGAs and general computers is that the array elements in the 

FPGA can operate simultaneously in parallel, whereas computers can only perform one function at a 

time. Not only does the parallel operation enable much higher speed, it also eliminates the need to 

switch tasks or contexts as with computers. For real-time applications, the main function of a 

computer operating system is to switch tasks to process interrupts and dispatch computer resources to 

the various tasks in the program. FPGA tasks are not switched because they are individually 

implemented in array circuitry that is always active. Thus FPGAs do not have operating systems and 

their associated reliability limitations caused by context switching times, memory overflow, virus 

vulnerability, and general operating system bugs. The overall complexity of an FPGA implementation 

is thus reduced because context switching issues have been eliminated. 

The parallel circuitry within FPGAs also produces an efficient pipeline action for signal processing 

applications. Complex DSP algorithms can be implemented with processing speeds greater than 

100 megasamples per second. FPGA vendors have also added specialized circuitry, known as cores, 

to facilitate DSP functions such as fast Fourier transforms (FFTs), finite impulse response filters, and 

hardware multipliers. 

FPGAs also have implementations of complete computers because some algorithms are not DSP 

oriented and are more suited to traditional computer processing. These implementations can be 

microprocessors with dedicated hardware or microprocessors defined using logic in the gate array. 

Gate array versions are called soft cores, and one example is the XilinxTPF

*

F MicroBlaze microprocessor. PT

 

TP

*

PTHwww.xilinx.comTH, accessed 2008. 
29 

Up to eight separate MicroBlaze microprocessors can be implemented on the larger Xilinx FPGAs. 

An example of a hardware microprocessor is a PowerPC microprocessor implemented with an FPGA 

on the same chip. Gate array resources, such as volatile memory, read-only memory (ROM), external 

memory interfaces, Ethernet circuitry, and general I/O can connect to the on-board microprocessor to 

make the chip a complete computer system. Computers on the FPGA can connect directly to the gate 

array logic, thus enabling the system to use the array for DSP and general logic and the computer for 

general processing. 

There are several software tools available for FPGAs. All FPGA vendors supply VHDL and gate 

logic hardware schematic compilers to generate configuration code for programming the device. 

Higher-level languages are also available for some FPGAs. MATLAB can perform desktop 

simulation on m-code software or create Simulink diagrams to test operation before compiling to 

VHDL code. Los Alamos National Laboratory has written the Trident compiler that translates C 

software into FPGA code. Extensive verification and validation (V&V) tools are also available for 

testing code prior to use. 

FPGAs can be useful for nuclear safety systems because of their high reliability, high speed, and 

conceptually simple implementation. Highly rugged, radiation hardened and reliable versions of 

FPGAs have been developed for space and military use. Several reactors in Japan have implemented 

safety functions with FPGAs. There are several reasons why FPGA systems can be very reliable. 

First, they can implement a complex system, complete with redundancy logic, on a single chip and 

thus reduce interconnects. Second, the implementation does not require an operating system that may 

have reliability limitations. Third, if the design is implemented solely in VHDL, obsolescence issues 

will be greatly reduced because some form of FPGA will always be available for implementation of 

the VHDL code well into the future. On the other hand, the great flexibility for programming FPGAs 

can be a concern for qualifying the devices for nuclear use. While VHDL code can be qualified, many 

FPGAs have unique hardware cores that will require their own qualification. Use of higher-level 

software languages such as C or m-code will invoke software quality assurance procedures for 

qualifying the code. It is also technically possible to implement computers on the FPGA complete 

with operating systems, which would require separate qualification. The various software tools, such 

as code generators, compilers, and V&V tools may also require qualification. 

FPGA’s have been recently deployed in a number of nuclear power plants. Olkiluoto-3 [(OL)-3] plant 

in Finland, for instance, employs an automatic hardwired backup system (HBS) that uses FPGAs. The 

HBS contains a small subset of the protection system functions, which include automatic actions 

needed to cope with certain design basis events. 

4.2.7 Field Programmable Analog Arrays 

FPAA devices are the analog counterparts of FPGA devices. The FPAA configuration is 

programmed by a digital memory that actuates an array of analog switches that connect operational 

amplifiers, resistors, and capacitors within the integrated circuit to form circuits performing specific 

functions. Typical circuits that can be implemented using the FPAA technique are multiplexers, 

integrators, and various filters. The frequency response of an FPAA-based design is in the range of 

1 MHz. One company that makes FPAA devices is Anadigm, Inc.TPF

*

FPT 

Interest in FPAAs has declined due to the ability to perform same functions in digital form using 

FPGAs. One proposed application for FPAAs is for redundant signal processing in orbiting satellites 

 

TP

*

PTHwww.anadigm.comTH, accessed 2008. 
30 

to recover from radiation damage to analog circuitry. Possible uses in NPPs would be to add 

redundancy to the analog processing circuitry in temperature, vibration, and radiation sensors. 

4.2.8 System on a Chip 

A SoC is an integrated circuit containing electronic components required to implement a wide range 

of functions and has the computational power and flexibilities to form the bases of an intelligent 

computing system. The main processing components of any SoC are the microprocessing unit, 

storage memory and PROM. A basic computer system capable of performing a wide range of 

computational tasks can be constructed by adding the necessary I/Os to the main components. 

Typically, the I/Os consist of (ADCs) to measure sensor inputs, digital-to-analog (D/A) converters to 

provide control signals, display driver circuitry, and data communications (Ethernet, RS232, 

keyboard, USB, radio links, etc.). Necessary support circuits, such as clocks, voltage regulators, and 

interrupt controllers are also included. More advanced versions include on-board circuitry capable of 

high-performance signal processing functions such as DSP and FFTs. 

SoC products are commercially available with different architecture complexities. An example of a 

simple architecture form of SoCs is the 8-bit PICmicro microcontroller chip manufactured by 

Microchip Technology.TPF

*

F This chip includes a microprocessor, PT random-access memory (RAM), flash 

memory for program storage, built-in clock oscillator, RS232 interface, interrupt controller, timers, 

and ADC, all in a small 6-pin package. An example of a more complex SoC architecture is the 

integrated circuit chip used in cell phones, which contains a transmitter and receiver, data encode and 

decode capabilities, audio processing, speaker and microphone interfaces, keypad input interface, and 

a liquid crystal display driver. 

SoC can be used in embedded systems to provide distributed, small-scale computing systems This 

would be advantageous for NPP I&C designs due to its computational power, speed, flexibilities, and 

low cost to incorporate into the design. SoCs can be very reliable because the single chip system has a 

low number of interconnects. The small size would also be helpful in reducing the amount of 

radiation shielding required in radioactive environments. However, the perceived difficulty in 

achieving 100% test coverage for microprocessor-based systems could hinder its widespread 

application in safety systems. 

4.2.9 High-k Transistor Technology 

One trend in electronic components technologies has been focused on miniaturization to achieve 

high-speed performance. This trend is popularly described by “Moore’s Law,” which foresees the 

miniaturization features and performance objectives for the component manufacturers.TPF

†

FPTThe 

International Technology Roadmap for Semiconductors (ITRS) predictsTPD

54DPT that in 2018 the high 

performance ICs will show an internal supply voltage of a few tenths of volts, an oxide thickness for 

metal-oxide semiconductor (MOS) technology of 0.5 nm, and components connected to the board 

with more than 3,500 solder balls for microprocessors and more than 6,000 solder balls for ASICs. 

Indeed, geometrical scaling has currently reached fundamental material limits where further scaling 

can only be realized by using new materials and/or device architectures. The fundamental problem is 

that the thickness of the SiOB

2B insulation between the transistor’s gate and the channel has shrunk from 

about 100 nm to 1.2 nm in state-of-the-art microprocessors. This thickness is only about 5 atoms (the 

 

T*THwww.microchip.comTH, accessed 2008. 

T†TGordon Moore observed that the market demand (and semiconductor industry response) for functionality per chip (bitTs, 

transistors) doubled every 1.5–2 years. He also observed that Microprocessor Unit (MPU) performance [clock frequency 

(MHz) × instructions per clock = millions of instructions per second (MIPS)] also doubled every 1.5–2 years. “Moore’s 

Law” has been a consistent macro trend and key indicator of semiconduTctor products for the past 30 years. 
31 

thickness of a silicon atom is about 0.26 nm). At this thickness, electrons can tunnel through the gate 

to the channel even when the transistor is supposed to be off. This leakage translates to excessive heat 

as well as power drain in systems such as laptops and servers. In fact, gate leakage has increased 

100-fold in the last three generations of transistors, as illustrated in XFigure 10X.TPD

55DPT 

To solve the gate leakage/excessive heat problem, Intel has developed a new high-k dielectric 

insulator and metal gate materials to replace traditional gate stacks based on SiOB

2B and poly-Si.TPD

56DPT

These materials will allow manufacturers to scale the existing CMOS 65 nm technology down to 

45 nm while maintaining the isolation required in cutting down on current leakage in the off-state. 

Figure 10. Gate leakage has increased 100-fold in the last three 

generations of transistors (© 2009 IEEE).X54 

This will in turn reduce power consumption and reduce the amount of heat generated by the leakage 

current. In fact, both versions of Intel’s Penryn microprocessors—the dual-core and the quad-core 

microprocessors—are the first commercial microprocessor to have features this small (i.e., 45 nm 

feature size). 

4.2.10 Multigate Transistor Technology 

Another innovation being explored by the semiconductor industry to increase the density of 

transistors on the same silicon real estate while still reducing the leakage problem is to build up, 

rather than out. 

Throughout their history, silicon transistors on ICs have remained basically flat (planar technology). 

The basic transistor used in microprocessors consists of the source, the drain, a channel between the 

two, and a gate. The source, drain, and channel are all in one plane; only the gate with its thin 

insulating layer protrudes slightly above this flat plane. Ideally, no current flows from the source to 

the drain when no voltage is applied to the gate. However, as transistors shrink in size, a small 

amount of (leakage) current continues to flow, thereby increasing power consumption, even with no 
32 

voltage applied. One of the new technologies being explored is to raise the source, channel, and drain 

out of the substrate.TPD

57DPT The gate is then draped over the channel, as shown in XFigure 11X. This technique 

effectively constrains the current to only the raised channel, and electrons no longer have a leakage 

path via the substrate. This three-dimensional (3D) transistor structure is called the FinFET and may 

become the IC construction technology in the next few years. 

Figure 11. One concept for transistors of the future 

(© 2009 IEEE).X57 This is a three dimensional 

 concept (see text), as opposed to the planar 

 technology currently used in CMOS 

transistor fabrication.

4.2.11 Other Emerging Integrated Circuit Technologies 

Recent developments in nanotechnology have generated much interest in shrinking the size of the 

memory storage element in a memory device, with an increase in the device storage density capacity 

per unit area. Various methods of operation (classical as well as quantum) have been proposed and 

studied such as SRAM, DRAM, ZRAM, FRAMs, flash, quantum dots, resonant tunneling devices, 

phase-change memory devices, single-electron transistors, magnetoresistive memory devices, 

molecular electronic switching devices, polymer-based devices and carbon nanotube 

nanoelectromechanical system (NEMS) switches. 

Other emerging technologies include biologically-inspired ICs: by using DNA molecules as scaffolds, 

scientists have created superconducting nanodevices that demonstrate a new type of quantum 

interference which can be used to measure magnetic fields and map regions of superconductivity. In 

the future, the technology could be generalized to produce semiconductor or other types of electronic 

devices. 

4.2.12 Radiation-Hardened Integrated Circuits 

Electronics used in aerospace applications, such as orbiting satellites, have been the leading driver in 

using radiation-hardened integrated circuits. For electronic equipment, the total dose absorbed 

onboard satellite is in the range of 1 Mrad from cosmic radiation while in orbit. 

Radiation-hardened electronics in the 300 krad to 1 Mrad total absorbed dose range are commercially 

available, including the most popular microprocessors such as the Pentium and the PowerPC. 

Aeroflex, Inc.,TPF

*

FPT is one of the many manufacturers of radiation-hardened products, with electronic 

devices capable of withstanding 1-Mrad total dose. Among these devices are logic ICs, 

microprocessors, FPGAs, analog ICs, motor control, and voltage regulators. The Actel CorporationTPF

†

FPT

manufactures a family of FPGAs for use in satellites that are hardened to 300 Krad total dose and 

 

TP

*

PTHwww.aeroflex.comTH, accessed 2008. 

TP

†

PTHwww.actel.comTH, accessed 2008. 
33 

have a single event upset (SEU) rate of less than 1 × 10P

–6P

 per day. Silicon Designs Inc.TPF

*

F has produced PT

a hardened MEMS accelerometer for use in safe-and-arm systems for missiles. 

In the past gallium arsenide (GaAs) technology was considered for radiation environments because it 

can tolerate doses in the 100 Mrad range. However, even though GaAs is more resistant than CMOS 

technology to permanent radiation damage, it has a higher SEU rate that makes it less suitable for 

digital control applications. Use of GaAs in digital electronics has decreased because of 

improvements in competing CMOS and silicon germanium (SiGe) technologies. However, there is 

still a strong market for GaAs amplifiers, which can be used in sensors in high-radiation 

environments. 

4.3 TECHNOLOGY RISKS 

Digital I&C systems at NPPs depend upon the vintage of the plant, where systems can either be 

newly designed for the next generation of plants or upgrades from analog to digital form. In both 

cases, the obsolescence of electronic components because of short product lifetime would result in 

applying new technologies in I&C systems during the lifetime of the plants. With each new 

technology, some unidentified failure mechanisms and failure modes may arise. In the following 

sections, some of the new technologies and their potential risks and failure mechanisms are discussed. 

4.3.1 Failure Mechanisms 

Reliability is one of the most important and challenging issues facing ICs in any application. With the 

ever increasing transistor densities and evolving IC technologies (e.g., high-k materials and multigate 

transistors), there are likely to be new failure mechanisms that were heretofore unknown. However, 

there are two basic failure modes in general: 

• functional failures—hard failures that cause permanent failure of the electronic circuits such that 

the IC cannot perform the intended function—and 

• parametric failures—soft failures where the IC is still capable of performing the intended function 

but not under all specified conditions; soft failures have no lasting damage but would result in 

corruption of stored data. 

XTable 1X shows typical IC failure mechanisms that can occur at different times during the circuit life.TPD

58DPT 

Among the failure mechanisms reported in XTable 1X, the most dominant ones are the following. 

• Time-dependent dielectric breakdown (TDDB)TPD

59DPT—the dielectric breakdown mechanism occurs 

when electron current flows through the oxide. The oxide gate is stressed when a voltage is 

applied to the gate; the resulting current flow directly or indirectly creates localized damage 

regions in the oxide. The dielectric breakdown occurs when damaged regions within the oxide 

layer make a conductive path between the electrodes. This can lead to both hard and soft 

breakdown. 

 

TP

*

PTHwww.silicondesigns.comTH, accessed 2008. 
34 

Table 1. Failure mechanisms occur at different times in product life (Ref. X58X) 

Occurrence Failure mechanism Cause StimuliP

a

P 

 Process charging Process-induced electrical overstress 

(EOS) 

V 

Constant failure rate Electrical overstress Electrostatic discharge (ESD) and latchup V, I 

Infant mortality Infant mortality Extrinsic defects V, T 

Infant mortality Logic failure Test coverage n/a 

Wear-out failure Hot carrier injection (HCI) e-impact ionization V, I 

Wear-out failure Negative bias-temperature 

instability (NBTI) 

Gate dielectric damage V, T 

Wear-out failure Electromigration Atoms move by e-wind I, T 

Wear-out failure Time-dependent dielectric 

breakdown (TDDB) 

Gate dielectric leakage V, T 

Wear-out failure Stress migration Metal diffusion, voiding T 

Wear-out failure Interlayer cracking Interlayer stress ∆T 

Wear-out failure Solder joint cracking Atoms move with stress ∆T 

Wear-out failure Corrosion Electrochemical reaction V, T, RH 

Constant failure rate Soft error N and α e-h pair creation Radiation 

P

a

PV = voltage, I = current, T = temperature, ∆T = temperature cycle, RH = relative humidity. 

• Hot carrier injection (HCI)P

49P—the high electric field near the drain end of the channel results in 

some electron or hole injection into the oxide (XFigure 12X). The injected carriers produce damage 

that reduces the transistor current. Eventually, the device becomes too slow. Unlike other failure 

modes, HCI can be worse at lower temperatures. 

Figure 12. Hot carrier injection degradation mechanism observed in MOSFETs.TPD

60DPT 

• Negative bias temperature instability (NBTI)P

49P

 for p-type metal-oxide-semiconductor field-effect 

transistors [p-MOSFET or positive metal-oxide semiconductor (PMOS)] and positive bias 

temperature instability (PBTI) for negative metal-oxide semiconductor (NMOS) transistors—a 

positive charge builds up at the channel interface of PMOS transistors under negative bias and 

high temperature conditions (positive bias for NMOS). This results in a threshold voltage increase 
35 

and the absolute drain current IB

DsatB decreases over time causing device instability and performance 

degradation. The effects of NBTI are of increasing concern as device sizes shrink to 0.13 μm and 

smaller and operating voltages decrease. 

• ElectromigrationP

49P—as known since 1961, electromigration results from the atoms moving 

because of collision and subsequent momentum between conducting electrons and diffusing 

metal atoms. Electromigration has become more severe as transistor dimensions have shrunk, the 

electric field applied to the gate oxide has increased, and the operating voltage has become lower 

(making a given threshold shift cause a relatively larger impact on the circuit behavior). All 

advanced fabrication processes that use PMOS transistors experience this effect. Electromigration 

issues affect aluminum, copper, and other polycrystalline metals. 

• Stress migration, also known as stress-induced void (SIV) formationTPD

61DPT—stress migration is the 

movement of atoms to relieve compressive stresses. For example, the differences in coefficients 

of thermal expansion lead to stress in metal lines. Stresses also occur from processing and/or 

electromigration. The stresses can be relieved by forming voids in the metal lines (the last part of 

the metal line break may result from electromigration). Low-k dielectrics have reduced thermal 

conductivity and strength and have poor adhesion properties that can lead to reliability problems. 

• Single event effects (SEEs), SEUs, single event latch-up (SEL)TPD

62DPT—the term “soft fails” has been 

coined to indicate spontaneous changes in digital information from radiation effects. High energy 

cosmic rays and terrestrial sources of radiation (e.g., low energy neutron interactions with P

10PB and 

radioactive impurities in packaging/solder both produce alpha particles) lead to SEEs in ICs. In 

SEUs, a particle creates a funnel of charge on the silicon wafer. This in turn injects a current 

pulse at the site of the strike. If the SEU charge is less than the “critical charge,” the data are not 

changed. However, if the charge is greater than the “critical charge,” an upset event occurs and 

the data are changed. Advanced technologies have an increased sensitivity to SEEs; reducing the 

voltage significantly or increasing the frequency increases the failures in time (FIT) rate. Latchup is a parasitic IC problem causing a part to draw too much current, permanently damaging the 

part. Decreasing size increases multi-event latching compared to single-event latching. Soft fail is 

widely used in the semiconductor industry, while SEEs and SEUs are used mostly by the military 

and in satellite electronics.TPD

63DPT

4.3.2 New Potential Risks and Aging Phenomena 

The solid-state electronics industry is characterized by relentless pressure to expand and improve 

functionality, reduce costs, and reduce design and development time. As a result, device feature sizes 

have shrunk to the nanometer range, as already discussed, and design life cycles of most commercial 

products are less than 5 years. This introduces new reliability concerns with regard to their 

application in NPP environments. These concerns include the following. 

4.3.2.1 New Aging Phenomena 

Some of the aging issues may arise from the following concerns. 

• Soft breakdown and proton migration in the thinnest gate oxides that should appear below 3 nm. 

Several manufacturers are likely to follow Intel’s lead in replacing silicon oxides with other 

materials with a higher dielectric constant. The introduction of new materials to existing 

technologies, however, will most likely result in new and unprecedented electrical 

characterization challenges. Consequently, different test methodologies will need to be identified. 

The degradation mechanisms and models will also be different from the conventional ones used 
36 

for silicon-based devices.TPD

64DPT Because the materials and the technologies needed in producing a 

new generation of devices are still in their early development phase, data on the aging behavior of 

these dielectrics are not readily available and will not be for some time to come. Therefore, to use 

high-k gate insulators to resolve transistor tunneling effects problems will certainly require new 

TDDB characterization.TPD

65DPT

• Use of copper (Cu) interconnecting wires and low dielectric constant materials instead of 

aluminum and silicon oxide may lead to new aging effects such as (1) polluting of the silicon by 

copper through diffusion, in spite of the barrier between them; (2) creation of holes between the 

copper and the barrier; (3) potential increase of electromigration in copper wires due to defects in 

the interfaces;TF*FT and (4) short circuits between copper wires due to electrochemical migration. It is 

obvious in spite of the technological advances and the continued research in the semiconductor 

industry that there are certain issues yet to be fully addressed such as the reliability of low-k

dielectrics and aging risk due to adhesion to the barrier layer. In summary, the present level of 

understanding of electromigration in copper/low-k structures and lead-free solder applications is 

insufficient.TPD

66DPT

• The lifetime of highly integrated packages such as BGAs, where connections to the printed 

circuits are made using solder balls under the component, is another concern. With this soldering 

technique, the high thermal dissipation in the complex circuits induces high-temperature variation 

and acceleration of the aging of the solder balls. As a result, the lifetime may be reduced. 

4.3.2.2 Sensitivity to Environmental Conditions 

Most likely there will be a higher sensitivity to environmental conditions, which typically exist in 

NPPs, that might lead to soft failures. The increase in sensitivity of electronic components to 

temperature and electrical overstresses (EOSs) may also become an issue. The likelihood of the 

following phenomena will probably increase as technology advances, which may present a new set of 

challenges to semiconductor manufacturers and users: 

• There is a relationship between the time for the oxide to break down and rise in temperature. The 

rise in temperature tends to accelerate the breakdown of the oxide. Furthermore, thickness of the 

gate oxide is another factor in accelerating the breakdown process, where thinner gate oxide 

causes the oxide to break down more quickly than normal. Therefore, temperature control 

measures inside and outside the electronic cabinets will be critical for future I&C systems. 

• An increasing sensitivity to rapid and low-level electrical stresses due to EOSs on the systems or 

to electrostatic discharges (ESDs). These stresses may create latent defects on the silicon die, 

which may decrease the remaining lifetime of the components. 

• Higher sensitivity to radiation can create parasitic currents in the silicon since highly miniaturized 

transistors may switch with lower transient current densities. Such interaction between radiation 

and silicon may lead to false transient signals in the components (SEUs) or to destruction of the 

components. To date, SEUs were only seen in aerospace applications or aviation electronics in 

airplanes. However, whereas a 90 nm technology SER benchmark had a best-in-class FITTF†F rate of T

 

TP

*

PTElectromigration remains one of the most important reliability issues in semiconductor technology. The change from Al to 

Cu for the metal gate electrodes has only delayed, not eliminated the threat. 

TP

†

PTThe Failures in Time (FIT) rate of a device is the number of failures that can be expected in one billion (10P

9

P

) hours of 

operation. This term is used particularly by the semiconductor industry. 
37 

195 FITs, a 65 nm technology SER had FIT rates up to 6,500 per megabit, scaled to New York 

City.TPD

67DPT

• NBTI can occur during burn in and during circuit operation at elevated temperatures.TPD

68DPT

4.3.2.3 Maintaining Quality 

Future technologies will require expensive tools, high skills, and experience to achieve highly reliable 

components. ITRS estimates that the cost to build a new manufacturing line will be about $10 billion. 

The increase of manufacturing costs will lead to a concentration of manufacturers. This phenomenon 

may accelerate the obsolescence of electronic components. 

A low quality manufacturing may also be encountered due to the fact that small or “minor” 

manufacturers will provide low performance components for industrial needs. These minor 

manufacturers may manage the fabrication process with a lower efficiency. Many low cost suppliers 

lack sophisticated quality systems, do not use statistical process control, or do not have International 

Organization for Standardization (ISO) certification.TPD

69DPT 

Low quality and counterfeit parts can and do make it into legitimate products and therefore have the 

potential of being installed in commercial off-the-shelf systems. “Counterfeiting” can be as simple as 

remarking scrapped or stolen and possibly nonworking parts or as complex as illegally manufacturing 

complete parts from original molds or designs. A bogus part may be relabeled to appear to come from 

a different manufacturer or to appear to be a newer or even an older but more sought after component 

than it actually is.TPD

70DPT 

According to the Alliance for Gray Market and Counterfeit Abatement, a trade group founded by 

Cisco, HP, Nortel, and 3Com to combat illicit trafficking in their products, perhaps 10% of the 

technology products sold worldwide are counterfeit. Whole servers, switches, and PCs have been 

faked, but more commonly, only one part in hundreds or perhaps thousands in an end product is 

bogus. 

Visually, it’s usually hard to tell the bogus part from the real one. Sometimes, a look-alike product is 

sold on the open market under a slightly altered brand name. The far more prevalent kind of 

counterfeit ICs are either sold as legitimate brand-name goods or become components in otherwise 

legitimate products. Counterfeiters often duplicate materials, part numbers, and serial numbers so that 

their wares match those of authentic products. Some examples of counterfeiting with wide 

distribution are given below. 

• In the fall of 2004, the military contractor L-3 Communications reported numerous failures with 

an IC chip bearing the Philips Semiconductors logo. Failure analysis revealed a thicket of 

anomalies, including missing, broken, or separated wire bonds, and in some cases no silicon IC 

(die) inside the package. Other customers who bought the Philips chips also complained about 

their shoddy quality. It turned out that the chips had all been purchased from an unauthorized 

reseller. They were indeed Philips ICs, but the batch had been scrapped as defective by Philips. 

• Police raided a suspected counterfeiter in China’s Guangdong province and found fake computer 

parts and documents worth $1.2 million, including packaging material, labels, and even the 

warranty cards to go with them. All parts were professionally labeled with the Compaq Computer 

Corporation logo. 
38 

• Capacitor electrolyte made from a stolen and defective formula found its way into thousands of 

PC motherboards, causing the components to burst and leak resulting in computer failures. The 

estimated cost of recovery from such failures was more than $100 million. 

• In 1998, relabeled 266-MHz Intel Pentium II chips as 300-MHz Pentium IIs began showing up in 

PCs. At the time the latter cost $375 apiece, while 266-MHz chips cost $246. Operating the 

lower-speed chip at a higher speed led to reliability problems because the chip ran hotter and was 

more likely to process instructions incorrectly. 

Such serious problems prompted Electricité de France (EdF) to institute plans to audit manufacturers 

supplying I&C systems to its plants in terms of the manufacturing process and the transportation of 

the electronic components. EdF believes that this knowledge needs to be shared between industrial 

and scientific partners from the nuclear area or from other industrial areas to facilitate the following. 

• Collection of failure data from the failed components, especially failures due to low quality 

manufacturing, component design issues, technology bugs, and aging mechanisms. The collected 

information is not only interesting for the modern component technologies but also for the 

already used components, 

• Sharing research costs. 

4.3.2.4 Increase in Maintenance Costs 

The increase in the number of leads on components may lead to difficulties in repairing printed circuit 

boards. Thus, it may be more feasible to discard the boards rather than attempting to repair them. 

Such an issue may increase maintenance costs. 

In other cases, the components cannot be repaired because of the manufacturing and assembly 

process. Examples of new package technologies where the highly integrated package will not allow 

any repair include (a) chips directly soldered on the circuit board (chip-on-board package) and 

(b) components interconnected with the circuit board via an array of solder balls below the package 

(BGA). 

4.3.2.5 Complexity Issues 

Electronic systems will be more and more difficult to test because of the high level of complexity of 

the components. The reliability proof will be very difficult to achieve.X

69X

Different platforms are expected to converge in the future owing to advances in manufacturing 

technology and higher integration density; therefore, the total number of platforms is expected to 

decrease. 

The growing system complexity will make it impossible to ship designs without errors in the future. 

Hence, it is essential to be able to correct errors after fabrication.X

54X

 In addition, reconfigurability 

increases reuse, since existing devices can be reprogrammed to fulfill new tasks. 

4.4 REGULATORY IMPACT OF MICROPROCESSORS AND OTHER INTEGRATED 

CIRCUITS 

The growing system complexity of semiconductor devices could make it more difficult to guarantee 

delivering future IC hardware free of errors. In addition, the successful development of high-k
39 

transistor ICs, and the potential for multigate transistor ICs, could revolutionize the IC industry but 

could also introduce new aging phenomena, higher sensitivity to environmental conditions (e.g., 

temperature and radiation), and other issues related to qualification methodologies. 

Failure modes and mechanisms for both current and emerging digital I&C technologies need to be 

characterized to assess whether current defense-in-depth strategies will need to be updated and 

whether any new failure modes can cause unforeseen or unknown system responses. This is 

especially important in light of fully digital I&C system upgrades in Gen III plants and the potential 

for advanced digital I&C application in Gen III+ and IV plants in the future. An understanding of 

failure modes at the system level (e.g., PLC) is the goal with regard to application in safety systems. 

However, such data may not be readily available, and an understanding of failure modes at the 

component level may be necessary to develop a failure data integration framework from module level 

to system level, contributing to an understanding of how a component level failure relates to the 

failure at the digital I&C system level. In addition to characterizing failure modes to inform the 

regulatory process, the use of “complex” devices such as FPGAs in safety systems also needs to be 

carefully reviewed because such devices have the potential to be reconfigured, and reconfigurability 

increases reuse and the potential for adversely affecting the execution of a safety function. Use of 

FPGAs in safety systems also brings into focus the issue of how much V&V should be required. 
Page Left Intentionally Left Blank 
41 

5. COMPUTATIONAL PLATFORMS 

5.1 OVERVIEW OF COMPUTATIONAL PLATFORMS 

A computing platform refers to a hardware architecture or software framework (including operating 

system, programming language, graphical user interface) that enables software to run. 

Consolidation, which makes it possible to use the same software and hardware components on a range of 

platforms, seems to be a trend in operating systems. Forms of consolidation include operating system 

families that span the range of servers, desktops, and embedded devices and operating systems that use 

consensus architectural concepts like deterministic processor scheduling. 

The commercial market for embedded devices such as cell phones is part of the driving force behind 

consolidation that extends server and desktop systems to embedded devices (e.g., Windows and 

Linux).The extreme form of this would be an operating system family which includes a vendor-certified, 

safety-grade, secure operating system for use in smart instruments in a range of industries beyond the 

traditional military and aviation industries. 

5.2 TECHNOLOGY TRENDS 

5.2.1 Processor Support for Virtual Machines 

ARINC 653, which stands for Avionics Application Standard Software Interface, is a standard for space 

and time partitioning in a type of system called “Integrated Modular Avionics.”TPD

71DPT ARINC 653 specifies 

how a computer system can be divided into partitions, each partition having its own memory and 

processor time allocations (XFigure 13X). Each partition runs one or more applications. The specification 

provides deterministic behavior and guaranteed resource availability. Another goal is to provide for 

software reuse by allowing a mixture of old and new software (functions) to run together. The idea 

predates the hardware support for virtual machines (VMs) and has now been adopted by many, if not 

most, of the operating systems vendors selling to the aviation industry. 

Safety-critical applications typically assign functions to deterministically scheduled time slots, dividing 

the single CPU among them so that the computer is doing just one function at a time. There would need to 

be some safety benefit to compensate for discarding this rule. The possible benefits are similar to the VM 

partitioning described above. First, a safety supervisory application could run parallel with the main 

safety function, performing a more sophisticated version of the watchdog timer’s job. Second, some 

diversity could be achieved by running parallel safety functions using different CPUs and different 

memory locations. 

5.2.2 Distributed and Multicore Computing 

Intel recently demonstrated an 80-core CPU.TPD

72DPT This thumb-nail-sized chip delivers 1.0 teraflops of 

performance and 1.6 terabits aggregate core to core communication bandwidth while dissipating only 

62 watts.TPD

73DPT It is purely a research project whose design is specialized for floating point performance, not a 

commercial product prototype. 

IBM’s Cell processor has launched in Sony’s PS3 [SCOP3].TPD

74DPT The Cell consists of a 64-bit PPE and eight 

synergistic processing elements (SPEs), loosely coupled through a coherent memory subsystem. The 

SPEs execute code sent to them by the PPE or another SPE and provide computational performance with 

greater flexibility than traditional fixed function ASICs. The SPEs provide efficient computation for a 

wide variety of applications including network processing, high performance computing, and graphics 
42 

geometry processing. Peak performance is more than 256 GFlops for single precision and 26 GFlops for 

double precision. 

The processors described above show that multiple cores, on chip, with high bandwidth communications 

between them, can achieve high performance with surprisingly low power and cost. They show the 

potential to run detailed plant simulations quickly on small, powerful computers if the simulation 

algorithm is adapted to the parallel architecture.TPD

75DPT,

TD

76DTP

Figure 13. A simple model of an ARINC 653 partitioned system. 

5.2.3 Operating Systems and the Embedded Devices Market 

Consolidation seems to be a trend in operating systems. Forms of consolidation include 

• operating system families that span the range of servers, desktops, and embedded devices; 

• operating systems that span hardware platforms; 

• operating systems that use consensus architectural concepts like deterministic processor scheduling; 

• operating systems that implement standards such as POSIX application program interfaces and 

Common Criteria for security; and 

• operating systems that use standards such as PCI buses, TCP/IP networking, and the FAT file system. 

Consolidations such as these make it possible to use the same software and hardware components on a 

range of platforms. 

The military and aerospace industries see themselves as increasingly smaller parts of the embedded 

devices market, with dwindling influence on the market. The commercial market for embedded devices 

such as cell phones is part of the driving force behind consolidation that extends server and desktop 

systems such as Windows and Linux to embedded devices. The extreme form of this would be an 

Partition 1 Partition 2 Partition 3 Partition N

VIRTUALIZING OPERATING SYSTEM

Inter-Partition Messaging, Processor Scheduling, Memory Management, etc. 

HARDWARE

Media, Communications, Clock, Interrupts, Memory Management Unit, Processor, 

etc. 
43 

operating system family which includes a vendor-certified, safety-grade, secure operating system for use 

in smart instruments in a range of industries beyond the traditional military and aviation industries. 

There are at least two major differences that separate the mass market and the most demanding industrial 

markets: guaranteed real-time response is required in the industrial market and Internet connectivity is 

required in the mass market. Convergence might occur as capabilities are developed that bridge these 

differences. For example, guaranteed response might become possible in mass market embedded devices 

by dedicating one or more CPU cores of a multicore system solely to safety-related tasks residing in their 

own VM (practically independent of other processes on the computer). For these and other reasons, 

civilian and military government agencies have reason to participate in the committees that set the future 

for embedded devices. 

5.3 REGULATORY IMPACT OF ADVANCES IN COMPUTATIONAL PLATFORMS 

More advanced computing platforms (e.g., those using multicore processors) and operating systems are 

more likely to be used, if at all, in control applications than in safety applications, which require more 

rigorous V&V. Safety-critical applications typically assign functions to deterministically scheduled time 

slots, dividing the single CPU among them so that the computer is doing just one function at a time. For 

many safety system platforms developed for new plants or upgrades, an operating system such as 

Windows, if used at all, is likely to be used to run an engineering tool that automatically generates the 

application software for downloading into the safety-related subsystem modules. This automated process 

eliminates human translation errors. However, the issue of a more rigorous V&V for the engineering tool 

becomes more significant because of the safety-related application. 

Several nuclear plant upgrades and new plants will use PLC-based platforms, some of them with 

embedded ASICs. Some of these platforms have already been approved [e.g., TELEPERM XS (TXS)]. 

Thus there is some experience base with regard to reviewing digital I&C safety systems for compliance 

with regulations. Current regulations require, with some exceptions, compliance with V&V procedures 

identified in IEEE Std. 7-4.3.2. It is likely that revisions of the standard will keep pace with advances in 

digital platform technology. However, continued attention to progress in this technology focus area is 

recommended so that exceptions to requirements in the standard can be made in appropriate regulatory 

guidelines. 

The computational platforms for digital-based systems in NPPs cover an extraordinarily broad range of 

devices. At the lower end, a digital device in a safety system might consist of a few logic devices in a 

PLC or a few elements on an ASIC. At this end of the spectrum, the design of the device resembles a 

function block layout and the implementation is strongly analogous to the wiring of an analog device. The 

“program” being executed is almost as simple as an analog device, “run when you are turned on.” The 

regulatory question then becomes, when does a digital device become so simple that it no longer comes 

under the heading of digital computer? Can simple devices be exhaustively tested and obviate the need for 

reliance on quality control through a process of software engineering as defined in IEEE 7-4.3.2? At the 

lower end of the spectrum, it seems obviously true that the device is more like conventional hardware and 

can be tested as any other hardware device under IEEE 603. The question is how to draw the line between 

simple devices and complex ones. Regulatory guidance for such systems and devices [e.g., FPGAs, 

complex programmable logic devices (CPLDs)] that are halfway between “simple” and “complex” are 

currently not as well defined. For example, Position 8 of Section 2, “Command Prioritization,” of the 

Interim Staff Guidance DI&C-ISG-04 requires a priority module design to be fully (i.e., 100%) tested. 

This refers to proof-of-design testing, not to individual testing of each module and not to surveillance 

testing.TPD

77DPT If the priority module is designed using a CPLD or a device of similar complexity, it may be 

very difficult, if not impossible, to prove that such a device has been fully tested. This is due to the fact 

that such a device typically also contains several memory cells so that the internal states are not as well 
44 

defined as a device containing only simple gates. If such a device cannot be fully tested, it seems that an 

appropriate route that amounts to “software” V&V on the device should include a review of the following 

documentation, in addition to demonstration of an extensive test coverage (functional testing): 

1) Behavioral (or pre-synthesis) simulation results (typically, a behavioral simulation is used to 

verify whether the design entry correctly represents the design requirements) 

2) Post-synthesis simulation results (simulation of the synthesized design is typically performed), 

3) Post-place and route simulation results, and 

4) hardware simulation results (hardware verification needs to be performed using the same input 

test vectors and procedures from the previous steps. Note that this is not functional testing of the 

completed module). 

At the high end of fully digital systems, safety system video displays have to present large amounts of 

data rapidly with graphics to aid in interpretation and recognition and must recognize and respond to 

operator inputs at a time scale that feels instantaneous, like conventional hardwired controls. Screens must 

redraw rapidly so that the operator can move from one display to another to get to needed information. 

These graphics applications challenge the high end multipurpose, microprocessor technology. These 

devices tend to draw from and benefit from consumer-grade software and electronics. The main problem 

with consumer-grade computer platforms is that the commercial marketplace values high speed and low 

cost far more than reliability. Consequently, the difficulty in using high end components for safety-grade 

video displays or any other applications that come up in the future is that commercial system software and 

design tools are “reliable enough” for commercial-grade work but would present an enormous challenge 

for acceptance under current standards for the nuclear arena. 
45 

6. SURVEILLANCE, DIAGNOSTICS, AND PROGNOSTICS 

6.1 OVERVIEW OF SURVEILLANCE, DIAGNOSTICS, AND PROGNOSTICS 

Bond et al.TPD

78DPT estimate that the deployment of online monitoring and diagnostics has the potential for 

savings of more than $1 billion per year when applied to all key equipment. Online monitoring is being 

implemented in new light-water reactor (LWR) plants such as Olkiluoto in Finland.TPD

79DPT New designs for 

advanced NPPs, such as those within the Gen IV program, will have much longer intervals (potentially 

4 years) between scheduled outages, and also shorter outages. Enhanced online monitoring and 

diagnostics will be essential in achieving such high performance and availability levels. 

Bond and DoctorTPD

80DPT indicate that advances will have to be made in several areas to move from periodic 

inspection to online monitoring for condition-based maintenance and eventually prognostics. These areas 

include sensors, better understanding of what and how to measure within the plant, enhanced data 

interrogation, communication and integration, new predictive models for damage/aging evolution, system 

integration for real-world deployments, and integration of enhanced condition-based 

maintenance/prognostics philosophies into new plant designs. 

Advanced gas reactors and Gen IV plants are expected to operate at much higher temperatures (between 

510°C and 1,000°C) than currently operating LWRs. Operation in this temperature range has the potential 

to introduce new degradation processes that have not been experienced in current reactors and thus are not 

well understood or accounted for in plant design. Even for currently operating LWRs, Wilkowski et al.TPD

81DPT

estimated that new degradation processes have appeared on average at a rate of one every 7 years. For 

“active components” (e.g., motor-operated valves), the majority of component failures are related to 

failure to operate when called upon to do so (e.g., valve not opening or closing on demand). The failure of 

passive components is dominated by failures associated with service degradation. 

In the nuclear industry, surveillance and diagnostics techniques have been (and continue to be) used for 

many different applications, such as loose-parts detection, core barrel motion monitoring, rotating 

machinery condition monitoring, instrument response time measurements, predictive analysis of failures 

in sensors and sensor lines, and motor current signature analysis. 

6.2 TRENDS IN SURVEILLANCE, DIAGNOSTICS, AND PROGNOSTICS SYSTEMS 

6.2.1 Basic Methods 

System surveillance (or monitoring) and diagnosis were historically developed in the aerospace industry 

because of the need for continuous operation of critical equipment in commercial and defense aircrafts, 

space modules in lunar exploration, space shuttles, and space stations. Over the past four decades, these 

technologies have been further developed and adapted in the process industries (petrochemical, food and 

beverage, pharmaceuticals, metals, pulp and paper) and the automotive, electronics, and medical sectors. 

The emphasis and applications of these technologies in commercial NPPs has increased at a constant rate 

since the accident at the Three Mile Island Unit 2 reactor. 

The following definitions apply to the following sections. 

• Equipment, sensor, device surveillance or monitoring refers to the tracking of degradation-sensitive 

parameters that are derived from measurements made on the specific component or subsystem. In this 

task we look for changes in the signatures of interest. Examples of such signatures include the 

following: residuals between the measured process variables and their estimated values using physics 

or data-driven models; various statistical parameters such as standard deviation, root-mean-square 
46 

(RMS) value, signal skewness, and crest factor; spectral domain parameters such as frequency 

bandwidth, RMS values at specified frequencies, and ratio of energies between two frequencies; and 

performance parameters computed from physics and/or data-driven models. 

• Diagnosis is performed to determine the cause of changes exhibited in the various signatures during 

surveillance and to isolate the devices that indicate incipient failures. Surveillance, fault detection, 

and isolation have increasing degrees of difficulty and require more information and knowledgebased expert systems to identify the root cause of impending failure. 

• Prognosis is concerned with the estimation of remaining useful life of a piece of equipment. Often 

referred to as life prediction, prognosis is the most difficult of the three modules, shown in XFigure 14X. 

Prognosis, combined with condition monitoring, is useful in planning maintenance and equipment 

replacement, increasing the reliability of devices, and aging and life-extension studies of currently 

operating plants. 

Figure 14. Block diagram showing the integration of surveillance, diagnosis, 

and prognosis modules in a nuclear power plant. 

POWER 

PLANT 

SURVEILLANCE 

SYSTEM 

DIAGNOSIS 

SYSTEM 

PROGNOSIS 

SYSTEM 

INFORMATION 

INTEGRATION

DECISION AND 

PLANNING 
47 

Some of the details of the methods and applications of reactor surveillance, diagnosis, and prognosis are 

given in references TD82DT–DDDDDDDDDDDDDDDDDDDDDDDDDDDDDDTD98DT. These methods are primarily classified as parametric and nonparametric 

approaches. The parametric approaches use either physics (first-principle) or data-driven models. 

Nonparametric methods use data compression techniques, either in the time domain or in the frequency 

domain. Surveillance and diagnostics systems using model-based (i.e., first-principle) techniques generate 

signatures that indicate the deviation of the measured values from their estimated values. When these 

deviations exceed a prescribed tolerance, it is an indication of an anomaly, either in the process or in a 

device, equipment, or sensor. Nonparametric techniques generally compare calculated signatures to 

baseline signatures. Deviations from prescribed values are indications of anomalies. Often a knowledge 

base, along with a rule-based expert system or an automated pattern classification technique, is used for 

fault diagnosis. 

6.2.2 Physics or First-Principle Models 

Physics models almost invariably use mathematical representations to describe a system or change of a 

system (e.g., a process). Representations that are derived directly at the level of established laws of 

physics within a set of approximations are called first-principle models. A representation that combines 

various physical models is called a multiphysics model. 

Surveillance and diagnostics systems using model-based (i.e., first-principle) techniques generate 

signatures that indicate the deviation of the measured values from their estimated values. When these 

deviations exceed a prescribed tolerance, it is an indication of an anomaly, either in the process or in a 

device/equipment/sensor. 

Multiphysics models are developed for PWRs and BWRs using mass, momentum, and energy balance 

equations. They are then validated against plant operational data. These high-fidelity models have the 

advantage of tracking the system under the assumptions used during the model development. Along with 

process measurements, the models are then used for process or equipment monitoring and isolation. The 

first-principle models are generally nonlinear and may be linearized, if necessary, about nominal 

operating states. 

6.2.3 Data-Driven Models 

These models are developed using measured process data. The measurements have two components: an 

actual process value and a fluctuating or wide-band frequency component. DC to low-frequency data are 

used to develop multivariate models in various forms. The objective is to characterize the relationship 

among a set of related process measurements. Care must be taken to restrict the use of the models for the 

operating regime for which they are suitable. Some are referred to as auto-associative models, where the 

input and the output variables are the same. These models have the advantage of monitoring a large 

number of variables simultaneously and tracking the mismatch between the inputs and the 

model-estimated outputs. Any deviation between the two is an indication of potential anomaly, which 

requires a more focused multiple-input–single-output model for isolating the defects. Both linear and 

nonlinear general polynomial models are used in this approach and have been highly successful in real 

applications. It must be noted that such techniques have been applied to both nuclear and fossil-fuel 

power plants. Group method of data handling (GMDH),X

89X

 auto-associative kernel regression,TPD

99DPT and 

principal component analysisX

93X

 are some of the approaches commonly implemented in data-driven 

modeling of plant signals. 
48 

An example of the data-driven modeling approach using GMDH is shown graphically in XFigure 15X. The 

hierarchical scheme of approximating a given output as a function of related inputs is performed by 

successive layers where each layer introduces increased complexity to approximate the measurement. 

XFigure 16X is an example of developing a model for the pressurizer level in a PWR as a function of hot-leg 

temperature, reactor power, and pressurizer pressure. The model was able to detect a small mismatch 

between the measured and predicted values of the level for a short time period at the beginning of the 

reactor start-up. 

Figure 15. Group method of data handling (GMDH) model that minimizes 

the error yB

measB – yBpredB for the case of m-inputs {xB1B, xB2B, ... , xBmB}.

Figure 16. Comparison of the measured (–) and model-predicted (+) 

values of the pressurizer level signal (%) during start-up 

of a pressurized-water reactor.
49 

A second form of the data-driven modeling uses stochastic time-series models for characterizing the 

property of wide-band data. It is often assumed that the random signals are stationary for a given 

operating condition. The frequency bandwidth of the signals depends on the type of signals being 

modeled. In a nuclear plant, the bandwidth of process signals (temperature, pressure, flow, level, etc.) 

is about 20 Hz. The bandwidths of neutron detector signals and vibration signals are much higher—at 

least up to 200 Hz. A commonly used time-series model is the auto-regression (AR) model. The 

univariate AR model is often developed for characterizing temperature, pressure, and flow signals. 

The model is then used for estimating both frequency-domain and time-domain signatures. Examples 

of online monitoring include response time estimation of process sensors and stability monitoring in 

BWRs using in-core neutron detector signals. The multivariate AR model has the advantage of 

establishing the cause and effect relationship among a set of stationary signals and is useful in 

detecting and isolating anomalies. 

6.2.4 Nonparametric Methods 

Nonparametric techniques generally compare calculated signatures to baseline signatures. Deviations 

from prescribed values are indications of anomalies. Often a knowledge base, along with a rule-based 

expert system or an automated pattern classification technique, is used for fault diagnosis. 

Data analysis techniques that estimate the signatures by compressing the measurements either in the 

time domain or in the frequency domain are often called nonparametric techniques. The signatures in 

the time domain are often statistical parameters such as mean value, standard deviation, RMS value, 

skewness, flatness, crest factor, zero crossings, etc. Monitoring is done by comparing the calculated 

signatures with baseline information. 

Frequency-domain analysis is performed by transforming the time signal to the frequency domain 

using Fourier transform. Efficient algorithms, such as the FFT are available for online computation. 

The frequency spectrum features are compared with baseline data for further diagnostics. This is a 

popular approach for monitoring vibration of reactor core internals and rotating machinery and for 

bandwidth monitoring of process and neutron detector signals. Often the compressed information is 

combined with pattern classification techniques for detecting and isolating anomalies in components, 

pumps, turbines, fans, etc. 

6.3 STATE OF THE ART OF DIAGNOSTIC AND PROGNOSTIC SYSTEMS 

Howard has recently provided an assessment of the state of maturity of diagnostics and prognostics 

technology in the nonnuclear industry.TPD

100DPT This is shown in XTable 2X. This table also reflects the general 

Table 2. Assessment of the state of maturity for diagnostic (D) and 

prognostic (P) technologies (Ref. X100X) 

Diagnostic/prognostic technology APP

a

P AP

b

P IP

c

P NOP

d

P

Basic machinery (motors, pumps, generators, etc.) D P 

Complex machinery (helicopter gearboxes, etc.) D P 

Metal structures D P 

Composite structures D&P 

Electronic power supplies (low power) D P 

Avionics and controls electronics D P 

Medium power electronics (radar, etc.) D P 

High power electronics (electric propulsion, etc.) D&P 

P

a

PAP = Technology currently available and proven effective. 

P

b

PA = Technology currently available, but verification and validation (V&V) not completed. 

P

c

P

I = Technology in process, but not completely ready for V&V. 

P

d

PNO = No significant technology development in place. 
50 

state of diagnostics and prognostics for applicable systems in the nuclear industry (e.g., rotating 

machinery, metal structures). In the nuclear industry, surveillance and diagnostics techniques have been 

used for many different applications, such as loose-parts detection, core barrel motion monitoring, 

rotating machinery condition monitoring, instrument response time measurements, predictive analysis of 

failures in sensors and sensor lines, and motor current signature analysis. A sample of the various 

applications follows. 

6.3.1 Redundant Sensor Monitoring 

If one of three redundant sensors degrades, simple logic can be implemented to identify the failed sensor. 

However, when there are only two redundant sensors, the task is not as straightforward. A technique to 

determine which of two diverging sensor measurements is correct would be of benefit to an operator who 

must choose which channel to use for input to an automatic control system. 

A redundant sensor calibration monitoring system was developed that can monitor as few as two 

redundant sensors. This technique merges empirical modeling techniques with independent component 

analysis (ICA) to produce a robust, low-noise prediction of the parameter of interest. If the variable of 

interest is not a controlled variable or if the control system is not a digital control system, the two 

redundant sensors must be augmented with an inferential sensor. The inferential sensor uses an empirical 

model with correlated signals as inputs. The two actual sensors and the inferential sensor are then input to 

an ICA-based redundant sensor estimation technique module. The advantages are reduced noise 

characteristics and robust prediction of variable errors through the use of ICA and increased stability due 

to the inferential sensor. Merging the principal-component-regression-based inferential prediction model 

with the ICA filtering algorithm produces accurate, low-noise predictions of the true process variable. The 

method produced predictions that contain all of the desired traits: accuracy, sensitivity, robustness, and 

low-noise. 

6.3.2 Acoustic Emission Analysis 

Acoustic emission sensors can be used for detecting the failures of check valves through measuring and 

analyzing the backward leakage. An acoustic emission sensor can identify the characteristic response 

frequencies of a failed check valve through an analysis of the test results. In one application a condition 

monitoring algorithm was developed using a neural network model to identify the type of the failure in 

the check valve. The monitoring algorithm can be used for the identification of the type of failure of a 

check valve without any disassembly work. 

6.3.3 Loose Parts Monitoring System 

NRC Regulatory Guide 1.133 requires reactors licensed since 1978 to include systems to detect parts and 

components that have become loose within reactor vessels and primary coolant systems. Many older 

plants also have these systems. However, many of these systems have given spurious alarms, failed to 

detect loose parts, and lacked diagnostic capability for investigating detected signals.TPD

101DPT 

Loose parts monitoring systems (LPMSs), in general, use a variant of impact theory for valid signal 

determination. The impact theory, also known as the Hertz theory, describes the impact of a solid sphere 

on an infinite metal plate. The theory works reasonably well provided that the diameter of the sphere is 

not large compared to the thickness of the plate and that the impact velocity is sufficiently small to avoid 

plastic deformation. The representative model is usually modified to include variable physical parameters 

that affect the impact wave propagation and detection.TPD

102DPT The parameters are identified based on the 

experimental data obtained with a known impact input that results in best-fit observed wave 

characteristics. 
51 

Wavelet transform and artificial neural networks (ANNs) show the potential to enhance LPMS 

performance by solving the tasks of noise cancellation, time of arrival detection, discrimination between 

real and faulty alarms, and loose metal piece mass determination. 

One example is a PC-based digital LPMS developed for the Maanshan NPP by the Institute of Nuclear 

Energy Research, Taiwan.TPD

103DPT The monitoring system uses a location estimation algorithm, which mainly 

implements time difference method with energy ratio as an auxiliary indication, and a mass estimation 

algorithm, which uses an ANN with fuzzy logic. The performance of the system was verified using 

simulated impact test data. The system was able to correctly indicate the impact region; however, 

statistical assessment indicated a 14.4% standard deviation in mass estimation for an impact mass of 

1.0 lb. The hardware in this particular system consists mainly of standard National Instrument modules. 

The application program was built using LabVIEW graphical programming software. For the location 

estimation, the time difference and energy ratio were used to infer the distance information. To determine 

the wave arrival time, short time RMS was used. Test results show this method is able to point out the 

regions of impact. The neural network with fuzzy linearization algorithm was applied to mass estimation. 

The back propagation architecture with 28 total input nodes, including one frequency ratio, one frequency 

center, and 26 linear predictive coding coefficients, was adopted in the neural network. The fuzzy 

algorithm is used to improve the linearity of the mass estimation. 

Improvements in LPMS will provide more accurate monitoring capability in terms of both pinpointing the 

impact location and determining the impact mass. 

6.3.4 Passive Monitoring with Micro-Electromechanical Systems 

A candidate approach to fault detection and isolation (FDI) in hydraulic, fuel, and pneumatic systems is 

the use of noise analysis techniques, which are passive in nature. Noise analysis has been proposed for 

detecting blockages, voids, and leaks in pressure lines. In NPPs, it has been shown that pressure sensing 

lines can become blocked and that noise analysis can be used to detect such faults. MEMS sensors and 

their associated algorithms can be used to automatically isolate blockage and internal leakage faults in 

pressurized systems. Although the same fundamental modeling and analysis technique can be applied to 

hydraulic, fuel, and pneumatic lines, the FDI analysis parameters must be specifically tuned to the 

particular system as the physical parameters (for example, viscosity, density, and compressibility) of the 

fluids differ. Presently the use of basic statistical descriptors such as RMS noise and zero-crossing rate 

monitoring for monitoring the health of the pressurized lines are being investigated. The ability to use 

fundamental noise signatures has the distinct advantage of facilitating FDI algorithm incorporation into a 

MEMS device to create an intelligent sensor. MEMS components are hybrid electrical and mechanical 

devices that combine mechanical microstructures with electrical processing circuitry onto a single die. 

Incorporation of the diagnostic algorithms into the sensing circuitry would provide the capability for realtime, passive condition monitoring of pressurized lines such as pipelines and transducer sensing tubes. 

6.3.5 Integrated Asset Management System 

Asset management can be described as maintaining equipment inventory to deliver maximum 

performance and service life at minimal cost. An integrated asset management system (AMS) provides 

the capability of predictive maintenance scheduling based on condition parameters of the field equipment. 

An important benefit of prognostics is that the equipment can be taken offline before it fails, and can be 

maintained or replaced, which usually increases plant availability and reduces maintenance cost. 

Modern field devices are usually equipped with a sensor module and an integrated diagnostics module. 

The diagnostics module can monitor the sensor condition and verify the validity of data. Once an anomaly 
52 

is detected, a predetermined set of instructions can be executed and the root-cause analysis can be 

performed. For a safety-critical component, this may require the commencement of an emergency 

operation regime. 

An integrated AMS system has three major components: (1) active field devices, (2) communication 

devices/systems, and (3) asset management software. Advanced AMS software can monitor performance 

and condition parameters of plant components and field devices, and provide guidance on plant spare 

component inventory. 

XFigure 17X shows a sample life-cycle management (LCM) strategy for a nuclear power plant with asset 

management as a component. LCM can be described as the process by which NPPs integrate operations, 

maintenance, engineering, regulatory, environmental and business activities that (1) manage plant 

condition (equipment reliability, aging, and obsolescence), (2) optimize operating life, and (3) maximize 

plant value without compromising plant safety. 

Figure 17. Asset management as part of life-cycle management (LCM) strategy.TPD

104DPT 

As seen in XFigure 17X, asset management in many aspects is as an indispensable component of life-cycle 

management. As listed under physical asset management, engineering, maintenance, ageing, and 

obsolescence management are important components to achieve improved plant condition. Condition 

Safety 

Optimum 

Operating Life 

Improved 

Plant Condition 

Maximum 

Plant Value 

Physical LCM

Asset 

Management 

Financial 

Asset 

Management 

Nuclear 

Asset 

Management 

Equipment 

Reliability 

 Engineering 

 Maintenance 

 Ageing Management 

 Obsolescence 

 Early Retirement 

 License Renewal 
53 

monitoring of plant components and field devices is becoming a major strategy for preventive 

maintenance (PM). The PM approach addresses failure probability and failure modes of critical reactor 

components. This is achieved by creating a list of equipment and components. The comprehensiveness of 

the list is a trade-off between the estimated increase in net present value of the plant due to investment 

and required capital cost for the necessary instrumentation and other infrastructure to implement the plan. 

Condition monitoring processes information from both field devices and sensors that are specifically 

deployed for each component. The information acquired from all sensor nodes is processed in a dedicated 

calculation node, fundamentally performing a detailed failure modes and effects analysis. The analysis 

algorithm may use artificial neural networks, fuzzy logic, and other parametric methods. A sample 

process algorithm proposed by EPRI is shown in XFigure 18X. 

Figure 18. Equipment condition monitoring plan proposed by EPRI.TPD

105DPT 

A significant advantage that can be gained with the online monitoring tool is that it can be integrated into 

the operations management system for advanced planning of repair or replacement and into the asset 

management system for continuous cost/benefit analysis for equipment upgrade. 

6.4 REGULATORY IMPACT OF ADVANCES IN SURVEILLANCE, DIAGNOSTICS, AND 

PROGNOSTICS 

Automatic surveillance offers tremendous new opportunities for plants to operate more reliably, test more 

frequently, reduce risk of latent failures, reduce maintenance costs, and reduce worker exposure—all of 

this at the low cost of digital monitoring systems. The issues from a regulatory standpoint are mainly 

concerned with when the surveillance system is applied to a safety system and the surveillance performs a 

Develop Equipment List 

for Consideration 

 Poll OLM Users 

 Identify critical equipment 

 Review typical OLM models 

Develop Equipment List 

for Consideration 

 Review EPRI failure data 

 Review NMAC failure data 

 Review EPRI PM bases 

 Discuss with manufacturers 

Develop Equipment List 

for Consideration 

 Decide instrument requirements 

 Develop desired instrument list 

 Establish benefits 

Develop Equipment List 

for Consideration 

 Link potential failures to instrument behavior 

 Develop Bayesian belief network for each failure 

 Test results on sample cases 
54 

required function under regulatory control based on Regulatory Guide 1.118.TPD

106DPT A number of fundamental 

questions emerge, as follows. 

1. Are there any subjective monitoring criteria that an expert adds to a manual surveillance that are lost 

in the automated surveillance system? Digital systems have extraordinary capabilities to monitor 

themselves and their environment to determine that the system is operating normally. Digital systems 

are also tireless and fast. However, the digital test performed is limited to the designer’s ability to 

anticipate all the symptoms of failure and nonfailure and provide a reliable sorting of the sample data. 

The human operator has enormous capability for subtle thinking and inference. This leads a human to 

cross-check anomalies even when the symptoms are not clearly indicative of failure. This deeper level 

of intelligences is difficult to duplicate in computer programming. 

2. Are the systems being monitored and their failure modes easy to recognize? Are the surveillance 

system’s failures easy to recognize? Can the operator accurately tell the difference between the failure 

of the surveillance system and the failure of the device it is monitoring? What are the percentages of 

false positive and false negative failures? Can these reliabilities be estimated in any way? A 

surveillance system needs to give confidence. A system that breaks or gives false readings only adds a 

distraction to an operator’s job. 

3. Does the presence of the automated surveillance system affect the reliability of the safety function? 

Usually the negative impact is not obvious. Typically, a surveillance system consists of a separate 

processor from the equipment that operates the safety function. The surveillance system is designed 

so that its failure does not affect the operation of the main safety function. However, certain types of 

diagnostics can affect the reliability. For example, a noise-based surveillance of a safety sensor may 

require a faster processor or communications system to give the minimum sampling rate needed for 

the test. The reliability of the safety function is diminished by selecting faster components. Typically, 

a diagnostic system is a data concentrator. The strongest conclusions about the health of a system are 

achieved by gathering all the data available about a system. This leads to interconnections to many 

other systems and the potential for failure related to the interface needed for the safety function. This 

type of requirement can increase the data burden on the safety function and decrease its reliability. 

4. How can the surveillance function be protected against a software fault that leads to a common cause 

failure to detect a failed protection system? The regulatory authority is currently struggling with the 

implications of diversity and defense-in-depth (D3) regarding digital protection functions. Logically, 

the same concern can be applied to surveillance software. The issue for diagnostic software is more 

difficult because diagnostic software is typically more complex in concept than a safety system. The 

issue from a regulatory point of view is not clear. D3 issues for surveillance systems have not been 

adequately considered to date. 
55 

7. HUMAN-SYSTEM INTERACTIONS 

7.1 OVERVIEW OF TRENDS IN HUMAN-SYSTEM INTERACTIONS 

In general human-system interface (HSI) technologies for design and evaluation have been divided 

into three main types. Tools that focus on rendering the operator and the interface in 3D space are 

typically tied to a computer-aided design (CAD) environment and focus on see, reach, and fit 

evaluations using anthropometric models of people of different sizes. These types of tools may also 

be linked to virtual environments. The second class of tools includes integrated design and evaluation 

criteria and guidance, which are typically drawn from existing industry standards such as IEEE 

1023TPD

107DPT and IEEE 1289TPD108DPT or guidance reports such as NUREG-0700.TPD109DPT These kinds of tools are 

often integrated with tools from the other two classes. The third class of tools uses human 

performance modeling to drive the design and evaluation of the interfaces. The modeling may be 

done at the task level or may involve modeling of the cognitive processes and detailed actions of the 

operator. They also sometimes include modeling of people with different capabilities or under 

different types of stressors. 

In the control room (CR) environment, one of the most significant changes in the last two decades has 

been the interaction of computers and digital electronic technologies for plant monitoring and control. 

There are numerous publications discussing the needs and challenges facing upgrading I&C for the 

nuclear plant industry in view of the problems associated with aging and equipment obsolescence and 

CR modernization efforts during the last decades.TPD

110DPT,

TD

111DTP

 Although noticeable progress has been made 

technologically and in regulatory areas related to applying digital technology in modernizing 

operating NPPs and in planning for new designs, more challenges remain and need to be addressed on 

the national as well as international level.X10 

CR design is undergoing rapid changes as more computerization and automation technologies are 

being developed and incorporated in the design process and design products. Advanced control room 

(ACR) concepts based on emerging and enabling digital technologies are being implemented in new 

plant construction and for modifying current operating plants. Use of advanced HSI technologies in 

ACRs, such as those used in the Lungmen Nuclear Power Project (LMNPP) under construction in 

Taiwan [e.g., flat panel displays for information and controls, video display units (VDUs) with touch 

screens, XFigure 19X], has more implications when it comes to plant safety because deploying such 

interfaces with safety systems affects the operator’s overall interaction with the system and the 

requirements for the operator to understand a more fully integrated main control room (MCR). 

As illustrated in XFigure 19X, as part of the human factors engineering (HFE) design, the main HSI 

design includes (1) allocation of tasks among workstations, (2) assignment of responsibilities to 

operating staff, (3) arrangement of workstations, (4) selection and prioritization of alarms and their 

integration into the overall control strategy, (5) consideration of the type and characteristics of 

displays to be used, (6) human factors V&V issues, and (7) development of operating and training 

procedures.X1 

Regulatory guidance has been established and can be used as guidance in reviewing human factors 

aspects as they are incorporated in the design process and in considering digital products used in new 

designs of NPPs and for modifying operating NPPs. NRC NUREG-0711TPD

112DPT is designed to provide 

guidance in assessing the effectiveness of human factors practices. The human factors engineering 

program review model developed by NUREG-0711 can be used while, at the same time, taking into 

consideration the continuing advances in digital technologies which in turn would influence new 

design concepts, methods, and tools used in HSIs.TPD

113DPT 
56 

In spite of the availability of published human factors design standards and guidance, they could be 

generic in nature and may not be fully applicable to all NPPs, and some variants may be necessary to 

address each NPP’s specific needs based on its operation. Westinghouse Electric Company 

established a comprehensive HFE program for the AP1000 NPP (1,100 MW) where the majority of 

the plant systems will be controlled, monitored, and supervised through VDU-based workstations.TPD

114DPT 

Figure 19. Lungmen Nuclear Power Project digital instrumentation and controls 

system design process (Copyright_ Feb. 2009 by the American Nuclear Society, La Grange Park, Illinois).P

112 

Task support systems (TSSs) are at the cutting edge of HFE, in industrial environments in general, 

and in NPP CR design in particular. TSSs will make an important contribution to the operability and 

usability of modern HSIs. They will facilitate the simplified abstraction of system processes, the 

reduction of complexity and volume of information, and the availability of procedural support during 

nonroutine conditions. 

The importance of TSSs is derived from three trends associated with the need to design advanced 

HSIs. The first is the implementation of advanced digital technology in process control and CRs, with 

emphases on a partial or complete elimination of hard controls in favor of computer-based or soft 

controls. The second is dealing with the enormous amount of technical information presented to plant 

operators to analyze and make decisions that could impact the plant’s performance and the need to 

reduce the amount of information through abstraction. Finally, there is a need to ensure the safety of 

the plant and operating personnel and to improve plant productivity and cost effectiveness. This 

includes guaranteeing effective operator performance during accident management. 

The principles of task support are not really new; they are basically an evolution of the familiar 

concepts formulated for computer-based procedures and advanced HSIs. It is emphasized that 

P&IDs 

SDDs 

LDs 

IODB 

System 

Design 

Hardware Design/Test 

Planning

Design Definition

Software Design

Coding

Software Design/Test 

Integration Test

Validation Test

FAT/DFAT 

SFRA 

AOF 

TA 

OER 

HFE 

Analysis 

HSI

DPs

DCTs

MCR 

Design

HFE 

Design 

MCR 

Mockup

GETS

Simulator

HFE 

V&V 

SAT

Acronyms: 

AOF – Allocation of Function 

DCIS – Distributed Control Information 

System 

DCT – Display Connection Table 

DFAT – DCIS Factor Acceptance Test 

GETS – GE Test System 

HFE – Human Factors Engineering 

HSI – Human System Interface 

IODB – Input Output Database 

LD – Logic Diagram 

MCR – Main Control Room 

OER – Operating Experience Review 

P&ID – Piping and Instrument Diagram 

SDD – System Design Description 

SFRA – System Function 

Requirement Analysis 

TA – Task Analysis 

V&V – Verification and Validation
57 

thorough task analyses are essential to determining how critical support functions will help in 

improving the effectiveness, efficiency, and satisfaction with which CR operators can perform their 

tasks. The development of a TSS for HSI opens up new possibilities for exploring the contribution of 

such facilities to the usability of the HSI, the improvement of operator performance, and overall plant 

performance and safety. 

7.2 THE STATE OF THE ART 

7.2.1 Physical Interface Technology 

7.2.1.1 Hand Held Computers 

The technology now exists to integrate maintenance, diagnostic, and operating procedures into 

wireless mobile computers equipped with various wireless networking capabilities such as Bluetooth 

Zigbee, and Wi-media. These wireless computer devices may be used to provide up-to-date and easy 

to follow procedures to personnel as they perform maintenance, failure diagnostics, surveillance, 

emergency operations, and many other tasks. For such applications, the computer must be 

intrinsically safe and capable of withstanding abuse, and it should be environmentally hardened for 

use in harsh environments. The computer must also be capable of supporting standard type operating 

systems for ease of use over a wireless connection. A high bandwidth secured LAN would also be 

required to support such systems. Several commercially available computers have the capabilities 

needed to meet these requirements. 

7.2.1.2 Direct Human Interfacing and Brain Plasticity 

Direct human interfacing and brain plasticity is an emerging technology with ongoing research 

focusing on enhancing human ability to process complex information while reducing the probability 

for human error. In essence, this technology focuses on compensating humans with damaged sensory 

and motor functions by allowing the brain to control artificial devices. Brain plasticity can be defined 

as an adaptation of the central nervous system to abnormal sensory functions by modifying its own 

structural organization and functioning. Such physiological phenomenon and recent advances in 

instrumentation technology for sensory substitution have prompted researchers to develop tools to aid 

persons suffering from loss of some of their senses, such as loss of sight and loss of hearing, by 

compensating for their sensory losses. 

The underlying principle in sensory substitution is transmitting information from an artificial receptor 

(such as camera for vision substitution or accelerometer for vestibular substitution) to the brain 

through the central nervous system. The brain would then interpret and manipulate the information 

resulting in providing the necessary action to restore the loss of sensory function.TPD

115DPT,

TD

116DTP

 The brainmachine interface (BMI) is a form of this technology that provides an alternative human-machine 

interface (HMI) in which the brain accepts and controls a mechanical device as a natural part of the 

body to provide a method for people with damaged sensory and motor functions to use their brains to 

control artificial devicesTF*FT. The feasibility of this technology was demonstrated by researchers at 

Brown University by implanting a four-millimeter square array of 100 electrodes in the area of the 

brain of a monkey that is responsible for issuing commands to move the monkey’s arms. The 

electrodes were used to track the brain signals responsible for the ability to move the arm from which 

a computer model capable of extrapolating the monkey’s arm movements was created and used 

ultimately in controlling a joystick in response to the monkey’s thinking about moving its arm. 

 

T*T HTUwww.ele.uri.edu/Cources/ele282/So3/Gabrielle_2.pdfUTH, accessed 2008. 
58 

Research results have been published describing use of artificial receptors such as cameras to 

compensate for vision impairment and accelerometers to compensate for bilateral vestibular loss.X15

Similarly, fingertip contact switch data are experienced as touch. This is true despite the fact that the 

same electrotactile interface is used to couple data to the tongue, irrespective of the sensor 

technology. It is far less susceptible to overload because the human perceptive process continuously 

updates what it needs to perceive and ignores the remainder, automatically and unconsciously. 

Because the process is experienced unconsciously, it is much faster than the cognitive interpretations 

that the operator must make with conventional interfaces. Using this interface to monitor data flows 

on a large computer network or an industrial process, an operator would avoid overload by 

unconsciously “tuning in” to the relevant aspects of the data flow, abstracting meaning from the 

subjective “feel” of the data flow, and doing so with far greater speed and reliability than is possible 

with conventional HMIs. Crucially, because it allows the operator a total experience of the process, 

he/she is able to detect patterns and relationships that would be ignored or discarded by conventional 

interfaces. 

The BMI technology allows the nervous system to experience an external object as if it were a part of 

the body. For example, a blind person using a long cane perceives objects (a foot, a curb, etc.) in 

his/her real spatial location, rather than in the hand, which is the site of the human-device interface. 

That power is seen in the ability to sense that a situation has changed before being able to identify the 

change. The capacity to connect with an engineered system in this way is enabled by an innovative 

technology for human-machine interaction based on Bach-y-Rita’s electrotactile BMI, a 

computer-aided medical prosthesis already used to restore lost human senses.X16 Unconscious 

integration into the system leads to anticipatory behavior. Since integration of the BMI and implicit 

cognitive processing enable the user to experience the meaning of practically any electronically 

generated data stream by direct sense perception, many areas will benefit from major applications of 

these two technologies of brain plasticity and cognitive process in the future. 

Unlike conventional HMIs, which incorporate a strategy of conscious response to individual data, 

direct coupling to the nervous system enables processing of the data stream as a whole and integrates 

it with anticipatory cognitive processes. Since this bypasses many cognitive processes that are 

vulnerable to overload, it benefits from the characteristic of the implicit systems that they are resistant 

to these kinds of capacity difficulties. Furthermore, it taps the power of unconscious cognition to 

make sense of ambiguous cues. The application of brain-plasticity-mediated sensory substitution 

requires a practical enabling technology. The enabling technology is a transducer that converts the 

electronic data from an artificial sensor to a pattern of electrotactile stimulation. A low resolution 

sensory substitution system can provide the information necessary for the perception of complex 

images. The inadequacies of the skin (e.g., low two-point resolution) do not appear as serious barriers 

to eventual high performance because the brain extracts information from the patterns of stimulation. 

It is possible to recognize a face or to accomplish hand-eye coordinated tasks with only a few hundred 

points of stimulation. An experiment with stationary tactile-visual sensory substitution displaying the 

tactile matrix on the subject’s back showed that blind subjects were able to bat a ball as it rolled off a 

table at a point that had to be predicted by the blind subject. 

7.2.2 Virtual Reality 

Virtual reality (VR) technology has advanced in the last decade and proved to be of great benefit to 

ACR designs and in modernizing CRs of operating NPPs due to the advantages it has to offer. VR 

provides CR designers with the tools to create a 3D model capable of simulating physical layout at an 

early stage in the design process. With the VR model, plant operators, HFE personnel, architects, and 

end users (from the utility industry) can be involved in the development process to provide their 

inputs throughout the design process.TPD

117DPT As in any design process, the final design is attained after 
59 

several design iterations, and with the VR modeling, these iterations can be made easier and definitely 

less costly than building mockups. Although VR development software is commercially available, 

some have opted to develop their own systems—for some obvious reasons (solvency of some of the 

companies offering VR software, product obsolescence, use of proprietary formats, software not 

flexible enough to accommodate special operational requirements). Recently, the Norwegian Institute 

for Energy Technology (IFE) in collaboration with EdF developed a 3D VR system focused on a 

human-centered design (HCD) including VR tools that can be used to provide an ergonomic design 

which can be evaluated by the operators. The VR system, known as Control Room Engineering 

Advanced Toolkit Environment (CREATE), is an interactive 3D technology capable of placing 

manikins inside virtual rooms and incorporating a set of 3D tools for measuring distances, viewing 

angles, and LOSs.PX

114X, 

X

116XP

 The capabilities of CREATE were evaluated using five review tasks from 

NUREG-0700.X109 The overall structure of CREATE and its associated tools are illustrated by X 

Figure 20X through XFigure 24X. Using VR technology made it possible for plant operators to be trained 

under normal as well as abnormal operating scenarios using the virtual environment that closely 

related to the actual physical setup without compromising safety. 

In addition, operators’ performance can be evaluated and documented. Remarkably, R&D in VR 

technology has not been limited to ACR design and operator training but has extended to other 

applications such as an interactive work planning and visualization and VR dose, where manikins are 

shown to perform decommissioning of contaminated plutonium glove-boxes in virtual reality.X

16X

 This 

concept can be extended to other complex tasks within the nuclear industry. 

Modern visualization technology can now be applied to improve human awareness of working 

environment, problem solving, and decision making in nuclear power generating stations and 

associated utility support organizations. The need for this technology in nuclear utilities is growing 

because of the vast amounts of data and information now available, which could overwhelm users 

with the HMIs widely used today and thus adversely affect their performance, leading to unsafe 

operating conditions. 

One promising approach to support user needs for usable information involves modern visualization 

technology. Information can be displayed in traditional two-dimensional (2D) graphics or a range of 

2.5-dimensional (i.e., flat images with the appearance of 3D) to four-dimensional (4D) graphics (3D 

images changing over time). More complex 3D and 4D VR representations may involve complete 

user immersion, such as provided by the CAVE (Cave Automatic Virtual Environment)TPD

118DPT VR 

system. The CAVE system permits one or more viewers to move around within a virtual space while 

wearing stereoscopic glasses or some other kind of human-machine device. The system uses sensors 

attached to the primary viewer to track changes in head and body positions. The visual representation 

of the virtual world is adjusted automatically to reflect the viewer’s current position and gaze. The 

observer may actively use traditional controls (e.g., mouse, keys, joystick) and less widely used 

methods (e.g., voice input and electronic gloves) to request information presentations. Visualization 

technology should be considered for high value functions in nuclear utilities. Adequate situation 

awareness, problem solving, and decision making are possible with 2D data and information 

presentation methods currently in use. 

More advanced visualization tools are also being developed and used to improve HMIs by providing 

much more realistic simulated environments for design, training, planning, and practice purposes. For 

nuclear engineers, technology to simulate everything from simple half-life measurement experiments 

to complete CRs is readily available and can be used with different platforms such as personal 

computers. What to an outside observer might look like a typical computer video game, to a nuclear 

engineer more closely resembles a simulated nuclear environment such as a radiation laboratory or a 

research reactor CR. Intended applications range from simple virtual tours of nuclear facilities for 
60 

outreach purposes, conducting virtual radiation related experiments, virtual facilities for improved 

human-machine interfacing, virtual facilities for optimum design to minimize maintenance and also to 

minimize replacement time for parts, virtual dose calculations, etc. A projection-based VR system 

such as CAVE, which surrounds the viewer with four (or more) screens, is suitable for these 

applications. A general-purpose program is being developed in C++/OpenGL to create virtual models 

of interest. The program is modular and allows development of components and their assembly. 

Further, VR may also be very useful in achieving educational and outreach goals of the discipline. 

 Figure 20. Overview of the CREATE system (Copyright_Feb. 2009 by the American Nuclear 

Society, La Grange Park, Illinois).P

118 

Figure 21. Layout Tool with the model library to the left, from which objects 

can be dragged into the scene (Copyright_Feb. 2009 by the American Nuclear Society, La Grange Park, Illinois).P

118P
61 

Figure 22. Distance measurement tool in action 

(Copyright_Feb. 2009 by the American Nuclear Society, La Grange Park, Illinois).P

118 

Figure 23. Evaluation of label legibility showing the height of the text and 

calculated range of legibility (Copyright_Feb. 2009 by the American Nuclear Society, La Grange Park, Illinois).P

118 
62 

Figure 24. Virtual control room (Copyright_Feb. 2009 by the American Nuclear Society, La Grange 

Park, Illinois).P

118 

Another interesting application of this technology is the virtual dosimetry tool, which provides online 

radiation visualization. The system receives radiation measurement data from a set of both fixed and 

wireless detectors and visualizes the radiation environment in real time, adapting as more data 

become available or radiation-level changes are detected. The spatial position of the wireless 

detectors and the operators are measured using a real-time positioning system. From this information, 

radiation maps are built and visualized inside a VR model of the work environment.TPD

119DPT The live 

radiation map may also be overlaid on real live video of the environment in an augmented reality 

setting, placing the radiation map where it belongs in the real environment. Live dosimetry systems 

are also being introduced to hospitals in Norway and Japan for use with advanced medical equipment. 

Further development of the VR technology has resulted in reviving an old research topic known as 

augmented reality.X19 Augmented reality can be simply defined as a technology in which a digital model 

or scene is merged together with a physical environment representing an actual setting of interest. An 

example of an augmented reality application, combined with VR, is the live dosimetry systems based 

on the Virtual Live Dosimetry tool, developed by IFE and licensed for use at Tokyo Electric Power 

Company in Japan. It is also being introduced to hospitals in Norway and Japan for use in conjunction 

with advanced medical equipment. In its initial development phase, IFE demonstrated the augmented 

reality capability by developing a 3D radiation distribution model that can be viewed by operators 

using a head-mounted display to guide them in navigating through a facility while minimizing 

radiation exposure. Future developments in the VR and augmented reality technologies are expected 

to take advantage of portable computing and wireless communications to provide NPP operators with 

augmented-reality-based devices that are robust and easy to wear or carry while focusing on the work 

to be performed.X19 
63 

7.2.3 Video Display Units 

The HSI for LMNPP is typical of Generation III+ I&C. VDUs with touch screens represent the main 

HSI in the CR, where operators can monitor and control plant equipment and systems under both 

normal and abnormal operating conditions. The HFE program model described by NUREG-0711X12 was 

used as the technical basis for reviewing the criteria for the digital-based design of the CR. The 

underlying strategy for the new CR is to deploy a VDU configuration to effectively distribute task 

assignments and workloads when accessing a large inventory of displays from a fairly large VDU 

location. 

The total number of VDUs in the operation area of the CR is 45, each equipped with touch screen. 

Forty-two of the 45 VDUs have the capability to provide monitoring and control functions and are 

distributed among the wide display panel (WDP) and the main control console (MCC). The remaining 

three VDUs, with only monitoring function, are located on the shift supervisor console. Out of the 

42 VDUs, 12 are used in safety systems, and 30 are used in nonsafety systems. Operating and 

controlling any of the nonsafety systems can be accomplished from any one of these display units, 

resulting in added flexibility in plant operation.X1 

LMNPP has about 1,000 displays and controls that may be distributed on the 45 VDUs. This 

introduces additional cognitive cost on operators for accessing the information by display navigation. 

One of the concerns is whether the operators can search through the screens under high stress 

conditions. On the other hand, presenting control and related information on VDUs is more 

convenient and gives more control to the operators. It was concluded that more resources need to be 

allocated to develop systematic and sound training programs that address the operator’s role, operator 

skills, mental modes, and VDU usability strategies.TPD

120DPT 

Figure 25. Lungmen plant simulator—a replica of the main 

control room (Copyright_Feb. 2009 by the American Nuclear Society, La Grange Park, Illinois).P

112 

7.2.4 Automation in Systems 

New approaches are proposed for designing future functional computerized HSIs. Research toward an 

HSI design based on a formal functional approach has been conducted on a simulator called Fitness, 

where an entire computerized HSI, including the information system, can be created. This simulator 
64 

has been designed in a way to allow, in real time, the level of automation of the simulated process to 

be varied. Automation systems can be widely diverse and used for many different applications. Some 

preliminary human factor tests have been performed on this simulator with licensed operators as an 

attempt to assess the optimum level of automation for future plant operations. Preliminary results 

show that there is more than one optimum level of automation, where the level of automation depends 

on many different factors, unmanageable at the design stage of the plant I&C and HSI. The operators 

themselves need to examine the possibility of managing the level of automation according to their 

online needs. Varying levels of autonomy during operation could be an alternative to defining a fixed 

automation level. 

7.2.5 Control Room Design 

The CR design has rapidly changed as more computerization and automation have been incorporated 

in the design. ACR concepts are being implemented in the commercial nuclear industry for new plant 

construction. Use of advanced HSI technologies in the ACRs has more implications with plant safety 

because implementation for safety systems affects the operator’s overall role (function allocation) in 

the system, the method of information presentation, the ways in which the operator interacts with the 

system, and the requirements on the operator to understand and supervise a more fully integrated 

MCR HSI. To design useful support systems, a design basis and a systematic framework are needed. 

Numerous support systems have been developed or are still under development. As MCRs evolve, 

more support systems will have to adapt to adequately support the MCRs. However, according to the 

evaluation results for support systems in several papers, a support system is not guaranteed to 

increase operator performance.X14 Some support systems could degrade an operator’s situation 

awareness capability and increase his/her mental workload. When several kinds of support systems 

are used or additional support systems are added to the same setting, a design basis is necessary to 

resolve efficiency and integration issues. 

Currently many modernization projects are concerned with updating NPP CRs. The different products 

and strategies being used address the diverse needs of CR modernization around the world. Past and 

current projects demonstrate a wide range of modernization approaches, including simple in-kind 

(one-for-one) HMI replacements, transition to hybrid CRs using combinations of video-based and 

conventional HMIs, and complete replacement with video-based CRs. 

One advance in CR modernization is the computerized operator support systems (COSSs) designed to 

enhance the NPP operator’s performance when making key decisions related to plant operation under 

normal as well as abnormal operating conditions. COSSs use computer technology to support 

operators in cognitive activities such as assessment and response planning. The main core of COSSs 

is a knowledge-based system, such as an expert system, which provides recommendations or 

warnings to personnel such as fault detection and diagnostics, safety function monitoring, plant 

performance monitoring, maintenance advising, and operator support for plant control. General 

guidelines for developing COSSs are described in reference TD121DT. These include consistency with task 

requirements, consistency with general HSI, interaction with ongoing tasks, critical information alert, 

minimizing querying of user, and graphic representation of rules. 

The intelligence provided by the expert system offers advantages such as (1) automatic checks which 

track operators’ actions and compare them to actions expected from plant procedures or another 

models; (2) automatic warnings based on current conditions, predicted consequences, or side effects; 

and (3) smart interlocks capable of blocking control actions that conflict with current plant 

configuration.TPD

122DPT 
65 

The integration of auxiliary systems should be a key issue, both with respect to usability and cost 

savings. Operators and maintenance personnel should be trained on the functions and capabilities of 

the COSS and the relationships between the displayed messages and the plant system states that they 

are intended to represent. 

The main HSI resources associated with CMFDD systems have been grouped under four major 

categories: process measurements and performance indices; alerts; supporting evidence; and 

accuracy, confidence, and certainty. A condition monitoring system should, to the extent possible, 

condense the information it generates into one or a few performance indices that give the operator an 

indication of plant (or subsystem) status at a glance. To minimize secondary tasks and distractions, a 

performance index should be visible to the user only while performing tasks for which the index is 

relevant. Alert information generated by a CMFDD system should be either integrated into the alarm 

system if intended to alert the user to the need to take immediate action, or it should be integrated into 

existing information displays if it is not intended to alert the user to the need to take action but only to 

indicate abnormal status of components or systems. When presented with alert information, the 

operator should be provided with a means for readily verifying the alert and with evidence supporting 

the conclusion reached by the COSS. This capability could ideally be integrated into the alert 

response procedures. The statistical accuracy (or error margin) of CMFDD numerical results 

generated by a COSS should be provided to the user together with an associated confidence level, and 

there should be consistency throughout the HSI in the choice of how to express statistical accuracy or 

error margins. 

Typical displays currently in use in computer-based CRs should be augmented with new displays 

designed to better meet the information needs of plant personnel and to minimize the need for 

interface management tasks (the activities personnel have to do to access and organize the 

information they need). The basic design of the displays for supporting monitoring, detection, and 

situation assessment are a hierarchy of displays at various “levels of abstraction” from high-level 

summary information to very detailed information: top-level overview displays suitable for plant 

monitoring, displays providing progressively more detailed information suitable for situation 

assessment in the event something is not normal, and navigation aids to enable users to quickly and 

easily move from higher-level displays to lower-level displays in the hierarchy. The key step in 

designing displays is defining the type of hierarchy to be used to organize and define the displays. It 

is not practical or even possible to develop specific displays for every conceivable task. Thus, 

guidance is needed to identify candidate tasks to be supported. Identification should be based on three 

main factors: human performance reliability improvements, efficiency improvements, and interface 

management reduction. Task-based displays can help support reliable performance by reducing the 

demands on human memory to remember information from one display to the next and by reducing 

the distracting effects of performing interface management tasks. Computer-based displays can 

support teamwork while helping to overcome some of the problems that were raised previously. The 

key elements of computer-supported cooperative work (CSCW) displays include common frames-ofreference for the entire crew, support for awareness of the activities of others, and availability of 

collaborative workspaces and tools for team interaction with CSCW displays. The new displays will 

enable the HSI to better support a broader range of user tasks while significantly reducing the need 

for crews to engage in distracting interface management tasks. 

Another technique for optimizing HSIs proposes the operation advisory system to aid cognitive 

processes of operators as a design basis of support systems for advanced MCRs. This will suggest 

appropriate support systems to aid activities of the human cognitive process and to integrate the 

support systems into one system obtaining better performance. The proposed system supports not 

only the task, but also the entire operation process based on a human cognitive process model. 

Operators’ operation processes are analyzed based on the human cognitive process model, and 
66 

appropriate support systems that support each activity of the human cognitive process would be 

suggested and help the whole operation process: monitoring plant parameters, diagnosing the current 

situation, selecting corresponding actions for the identified situation, and performing the actions. 

Results show that operator support systems are helpful for reducing operation failure probabilities of 

operators, having a greater effect on less skilled operators than for highly skilled operators. The 

results also show that the effect of independent support systems is less than that of integrated support 

systems, indicating better human performance may be obtained by integrating support systems based 

on the operators’ cognitive processes. 

7.2.5.1 Minimum Inventory Issue 

In modern CRs that use digital technology, the primary interfaces used by the CR operators are based 

on selectable displays and controls as opposed to the fixed, dedicated display and control interfaces of 

earlier designs. There are several factors that stipulate minimum-inventory HSIs: IEEE 603-1998TPD

123DPT

requires that qualified, safety-related HSIs must be provided for accident mitigation, to achieve safe 

shutdown, and for post accident monitoring; ANSI/ANS-4.5-1980TPD

124DPT delineates criteria for 

determining the variables that the CR operator should monitor to ensure safety during an accident and 

the subsequent long-term stable shutdown phase; IEEE Std. 497TPD

125DPT provides relevant I&C system 

design criteria; and Regulatory Guide 1.97, Rev. 3TPD

126DPT provides a comprehensive list of variables to 

monitor. 

The definition of minimum inventory has been a topic of discussion for a while. A number of 

regulatory guidance documents such as NUREG-0711X

112X

 address the subject, and NUREG-0800,X

44X

Chapter 18, defines this concept as “complete set of HSIs needed by the operators to perform their 

tasks based on task analysis.” In earlier advanced LWR designs, the term was referred to as either “a 

minimum set of fixed-position or spatially-dedicated HSIs” or “HSIs needed in the case of failure of 

the HSIs normally used by the operators.” EPRI prepared a draft report to resolve the discrepancy on 

the term as well as to serve as guidance for industry,TPD

127DPT where the term is defined as “the HSIs that are 

needed beyond the nonsafety, selectable, computer-driven HSIs used by the operators and typically 

driven by a distributed control system.” These HSIs include the following. 

• Spatially dedicated, continuously visible displays driven by the nonsafety control and information 

system (e.g., a flat panel display that shows alarms in fixed positions, such as a tile-replica 

display). 

• Safety-related HSIs (e.g., qualified discrete digital or analog/hard-wired controls and indicators). 

• Non-safety-related HSIs that are independent of the main control and information system that 

drives the operator workstations (e.g., discrete controls and indicators and/or computer-based 

HSIs). 

X

XFigure 26X shows sample minimum-inventory HSIs that include both plant safety and nonsafety 

systems as itemized above. 

The minimum-inventory issue was recently addressed in the Interim Staff Guidance DI&C-ISG-05 

Rev. 0.TPD

128DPT The NRC staff position requires that the minimum inventory of HSIs should be developed 

for the MCR as well as for the RSR. 
67 

Figure 26. Different types of minimum-inventory HSIs. 

7.3 REGULATORY IMPACT OF HUMAN-SYSTEM INTERACTIONS 

There are many evolving design and evaluation tools that can optimize the design of HSIs and speed 

up their evaluation. All are based on computer software technologies. Many of these tools are being 

developed outside of the nuclear power industry. It is widely accepted that poorly designed HFE 

systems contribute to poor human performance, increased errors, and reduced human reliability.TPD

129DPT In 

addition, under degraded or emergency conditions, poor HFE design can delay or prevent corrective 

action by plant operators. The perfect CR layout, with attendant perfect operator interaction and 

allocation of human-machine function has not yet been developed. Even if such an ACR had been 

developed, the tools to confirm its performance capabilities have not yet been developed. It is 

therefore in the interest of improving and verifying the efficacy of ACRs that research continues in 

the three major areas of tool development: measurement tools for physical human interface; humanmachine interface and interaction design criteria and guidance, especially for allocation of functions 

in highly automated control rooms; and functional simulation modeling, including human 

performance modeling. 

SDCV HSIs Driven by NonSafety C&I System Independent, Non-SafetyRelated HSIs 

Non-Safety, Selectable HSIs 

Driven by Non-Safety C&I 

System 

Safety-Related HSIs 

Discrete 

Indic’s & 

Controls 

Redundant servers hosting 

applications used by HSIs 

connected to the C&I system

Reliable, highly faulttolerant, non-safetyrelated C&I system and 

associated data networks

Plant Safety Systems 

Discrete 

Indic’s & 

Controls 

Group-View 

Display 

SDCV 

Plant Non-Safety Systems 

MI MI MI

MI 

Different types of minimum 

inventory HSIs – HSIs provided in 

addition to the non-safety-related, 

selectable HSIs normally used by 

the operators for plant monitoring 

and control

SDCV HSIs Specially-dedicated, continuously visible Human-system interfaces – as used 

here, these are controls, displays and 

alarms 

Capability can be provided to 

monitor and control non-safetyrelated systems from the safetyrelated HSIs with suitable isolation to 

ensure they can still fulfill their 

safety-related functions if the nonsafety-related C&I system fails 

Some designs provide control and 

monitoring of the safety-related 

systems using the normal, nonsafety-related HSIs with features 

provided to ensure that the nonsafety-related HSIs cannot defeat 

needed safety functions 

C&I Control and Information 
68 

Digital data acquisition and display have the potential to present an ever increasing flood of 

information to plant operators causing overload and perhaps masking the most relevant information. 

An overloaded and confused operator can lead to inappropriate and detrimental actions.TPD

130DPT 

In recognition of the downside of digital computer-based systems in the control room, NRC has 

issued an interim staff guidance for human factors in digital I&C systems as a guide to determining 

how a licensee may satisfy NRC regulations.TPD

131DPT 

Some of the human interface technologies such as VR have already shown capability in the design 

stages. To reduce time and resources during the evaluation (V&V) stage, continued development of 

computer assisted tools should be encouraged. Developers of evaluation tools should be careful not to 

simply modify existing software from the design to evaluation environment. Some degree of 

independence and separation is needed to prevent built-in blind spots to systematic errors that might 

exist in the design tool software. 

Flat screen video displays have invaded much of the industrial controls environment both as displays 

and as control interfaces, through touch screen technology. Consideration as to the robustness of these 

displays and controls is needed for the nuclear environment (e.g., seismic stability). Further, because 

of the relative ease of installing flat panel displays, much analysis is needed by the designers to prove 

that operators are able to use them without overload or confusion. The development of well integrated 

control rooms with such displays and controls requires much research and simulation as well as 

appropriate regulatory guidance. 

The trend is to continue along the path to automation. Because there may be no optimum level of 

automation, individual licensees will vary in their allocation of functions to operators and 

computer-driven systems. For any given plant, even the level of automation may regularly vary 

depending on plant operating conditions and the training/skill of the operator. The levels of 

automation in various situations may be selected by the operator depending on the level of attention 

needed for other tasks. Guidance and general criteria given in the Interim Staff Guidance concentrate 

on automation of procedures. Hands-off automation for start-up and shutdown of plant systems is not 

covered by the existing guidance. Additional guidance related to function allocation and automation 

is needed for the licensee. 
69 

8. HIGH-INTEGRITY SOFTWARE 

8.1 OVERVIEW OF SOFTWARE TRENDS 

The term “high integrity” implies a specific characteristic of the software in terms of reliability or 

dependability that requires that the software must be developed using special techniques. The safety 

requirements of military, aerospace, and transportation applications, due to the consequences of 

software failure, continue to drive development of ever-increasing levels of quality and reliability for 

software. The international standard for describing the method of selecting, implementing, and 

monitoring the life cycle for software is ISO 12207.X

137X

 There are a number of models adopted from 

organizational and business management methodologies, such as the Capability Maturity Model 

(CMM) and Six Sigma. ISO 15504TPD

132DPT also provides a framework to establish a mode for process 

comparison. 

Although advances in software engineering have not kept pace with hardware, continuing evolutions 

and new methodologies in high integrity software should continue to be tracked because they have the 

potential to reduce the probability of CCF in digital systems. The present regulatory position is that 

software cannot typically be proven to be error-free and is therefore considered susceptible to CCFs if 

identical copies of the software are present in redundant channels of safety-related systems. The 

current mitigating strategies to cope with CCFs are to apply various diversity measures and a 

defense-in-depth philosophy. These measures, along with a highly reliable software development 

strategy, can reduce the probability of CCFs to an insignificant level. 

8.2 SOFTWARE DEVELOPMENT FOR SAFETY CRITICAL APPLICATIONS 

Software design, specification, development, and implementation are quintessentially nonmechanical 

and noncybernetic processes. Thus, systems engineering is one means by which the semantic 

difference between an expert’sTPD

133DPT understanding of process or functionality and a digitally valid, 

reliable, and dependable specification of that functionality is minimized.TPD

134DPT Fidelity to as-built 

physical systems in digital form ensures that physics is not virtually violated. For mission-critical and 

safety-critical functions, the semantic difference relationship must not only be minimized, but that 

expression must be very highly correlated and corroborative. Modern systems engineering 

environments are constructed to ensure formalism and discipline improves the necessary 

correspondence, the traceability of that correspondence, and the proof that the differences are 

minimal. However, once the model is established, the software functionality requirements and 

constraints must be identified and documented. In addition, the burden of proof that the specification 

satisfies all of those requirements and constraints rests with the software developer.TPD

135DPT 

In the software life cycle, there are a number of methods which support formalism.TPD

136DPT The discipline 

and corresponding methods and techniques associated with the hazard and safety analyses needed to 

address all aspects of safety critical NPP systems also exist. Some of these methods are included in 

XTable 3X. Each such software formalism is specific to target aspects of the software life cycle and none 

are comprehensive or deterministic to success in minimizing the semantic distance between expert 

model and specification. 

Modern computer hardware systems have capacities that far exceed mastery by contemporary human 

experts, and those capacities continue to increase not linearly but according to the multiplying 

consequences described by Moore’s Law. Digital systems thus represent a means, which must be 

controlled in NPP applications, for both complicated and complex functions. Digital systems are 

potentially complicated due to the capability to absorb many and large functions and processes. 
70 

Table 3. Example formalismsP

a

P

 for digital safety systems development 

Formalism Phase of software 

development Processes Products

Fault avoidance 3⁄4 Concept 

development 

3⁄4 Maintenance 

=Architecture, design; 

requirements; measures 

of performance; 

specification document 

Fault elimination 3⁄4 Concept 

development 

3⁄4 Maintenance 

 Detection 

 Removal 

Fault tolerance 3⁄4 Operations 

Fault evasion 3⁄4 Operations  Observation, ID 

anomalous properties 

=Compensating features 

Reliability analysis 3⁄4 System design 

3⁄4 System 

development 

 Operations research 

 Systems integration 

=Fault-consequence 

relationships; 

=Operational environment 

assumptions 

Management and 

procedures 

3⁄4 All phases  Dedicated; 

independent, 

professional analyst 

=Documentation; 

independent system 

safety responsibility 

Life-cycle models and 

safety life-cycle models 

3⁄4 All phases  Rigorous support to 

management for 

defining project 

phases and 

deliverables 

=Software safety plan, 

hazard log; Usafety caseU 

Hazard analysis 3⁄4 All 

developmental 

phases 

 Unsafe state 

identification; 

 Risk evaluation; 

 Tradeoff analyses 

=Measures to eliminate or 

mitigate. Make tradeoffs 

explicit 

=Documentation of 

acceptable hazard states 

and justification 

Techniques of hazard 

analysis 

3⁄4 Respective 

phases of life 

cycle 

 Reviews and walk 

throughs 

 Lessons learned check 

lists 

 Hazard and operability 

analysis 

 Failure modes, effects, 

and criticality analysis 

 Failure modes, effects 

analysis 

=Cause-consequence 

articulation; 

=System definition, 

functions, and 

components; 

=Component failure modes 

and respective causes; 

=Corresponding failure 

mode effects; 

=Conclusions and 

recommendations 
71 

Table 3. (continued) 

Formalism Phase of software 

development Processes Products

Additional techniques for 

hazard analysis 

3⁄4 Specific 

purposes at 

respective 

phases of life 

cycle 

 Probabilistic risk 

analysis 

 Gathered fault 

combination method 

 State-space methods 

 Fault trees analysis 

 Event trees analysis 

 Cause-consequence 

diagram method 

 Petri nets 

=Quantitative 

determination the hazard 

will be realized 

=ID fault combinations for 

systematic analysis of 

systems sets interacting 

=ID operating and failure 

states of repairable 

systems 

=ID events and 

combinations that 

progress to undesirable 

circumstances; and 

respective interactive 

logic 

=ID event sequences and 

respective, potential, 

consequences 

=Combination of fault 

trees and event trees 

=Timing constrained safety 

analysis 

P

a

P

“The value of formal methods is that they provide a means to symbolically examine the entire state space of a digital 

design (whether hardware or software) and establish a correctness or safety property that is true for all possible inputs.” 

Curator and Responsible NASA Official: HTC. Michael HollowayTH last modified: 31 January 2006 NASA Formal Methods 

Web Site http://shemesh.larc.nasa.gov/fml. 

Digital systems are complex because they can exhibit wholly unanticipated behavior, and because 

they implement pure concept, they are not bound by laws of physics. Since they are constructed by 

human endeavor, digital systems are assumed to be flawed through the unintended insertion of faults. 

It is this combination of attributes, almost certain to be exhibited in the right circumstances, that 

dictate that digital systems construction and implementation must be conducted in ways to protect 

against failure consequences. The means and methods of construction and implementation are, 

themselves, the means by which dependability and reliability can be ensured. Modern technology 

exists to accomplish control through methods which, when properly executed, can objectively ensure 

control is maintained and validity of operation is reliable and dependable in digital system 

functionality supporting even safety operations of NPP processes. Strategies exist to ensure these 

methods are robustly applied, but they represent a paradigm shift in conventional approaches to the 

design and development of digital systems. 

8.3 COMPUTER SOFTWARE DEVELOPMENT AND THE EMERGENT TECHNOLOGY 

WHICH SUPPORTS IT 

A growing number of software development organizations implement process methodologies. The 

international standard for describing the method of selecting, implementing, and monitoring the life 

cycle for software is ISO 12207.TPD

137DPT 
72 

• The Capability Maturity ModelTPF

*

FPT is one of the leading models. Independent assessments grade 

organizations on how well they follow the CMM-defined processes, not on the quality of those 

processes or the software produced. ISO 9000 is the accepted standard for describing formal 

organizing processes with documentation. 

• ISO 15504, also known as Software Process Improvement Capability Determination (SPICE), is 

a “framework for the assessment of software processes.” This standard is aimed at setting out a 

clear model for process comparison. SPICE is used much like CMM and CMMI.P

* P

It models 

processes to manage, control, guide, and monitor software development. This model is then used 

to measure what a development organization or project team actually does during software 

development. This information is analyzed to identify weaknesses and drive improvement. It also 

identifies strengths that can be continued or integrated into common practice for that organization 

or team. 

• Six Sigma is a methodology to manage process variations, and it uses data and statistical analysisTPF

†

FPT

to measure and improve a team’s or organization’s operational performance. Six Sigma is a 

method to identify and eliminate defects in manufacturing and service-related processes. 

However, Six Sigma is manufacturing-oriented, and further research on its relevance to software 

development is needed. 

The most important task in creating a software product is extracting the requirements of software 

performance. Users typically know what they want but not what software should do, while 

incomplete, ambiguous, or contradictory requirements are recognized by skilled and experienced 

software engineers. Frequently demonstrating live code may help reduce the risk that the 

requirements are incorrect. Model Driven Development is one modern means by which this 

demonstration can take place, live, without the need for code development. The live model, derived 

from requirements, can also demonstrate block integrity and version independence, expediting the 

generation of versions. 

• Specification is the task of precisely (and rigorously) describing the software to be written which 

matches and/or further differentiates requirements. In practice, most successful specifications are 

written to understand and fine-tune applications that were already well-developed, although 

safety-critical software systems are often carefully specified before application development. 

Specifications are most important for external interfaces that must remain stable. This is 

particularly true for safety/nonsafety interfaces. It is the means by which control of reactor 

processes can first be addressed consistent with safety, the reactor design basis, analysis 

guidelines of NUREG 6303, and design vulnerabilities to CMF. Modern tools exist for 

nominating requirements and tracing their evolution, pedigree, traceability, and satisfaction. The

Dynamic Object Oriented Requirements System is one example, and there are many others.

• Software Architecture refers to an abstract representation of the system. Architecture is concerned 

with making sure the software system will meet the requirements of the product and ensuring that 

future requirements can be addressed. The architecture step also addresses interfaces between the 

software system and other software products, as well as the underlying hardware or the host 

operating system. The Open Group Architecture Framework is one standard, but it is largely 

directed at enterprise architecture. The Department of Defense Architecture Framework is an 

emerging federal standard tailored to command and control. 

 

TP

*

PTCMM is gradually being replaced by CMMI, Capability Maturity Model Integration. 

TP

†

PTThe maximum permissible defects is 3.4 per 1 million opportunities. 
73 

• Architecture Products are those graphical, textual, and tabular items that are developed in the 

course of building a given architecture description. Each product describes characteristics 

pertinent to scaled aspects of the architecture. These products serve as software system design 

tools directed at the ultimate software to be developed. These products provide a means by which 

software development diversity can be implemented and maintained throughout the life cycle of 

each development. Through modern methods, the generation of code can be pedigreed and the 

diversity of version can be protected. Software architecture and its products may be the last 

commonality of version diversity and the formal means by which diversity independence can be 

created and assessed. Products are essential to both knowledgeable application of programming 

methods and defense-in-depth implemented in the coding process.

• Implementation (or coding) represents the reduction of a design to code (as reviewed above), and 

this may be the most obvious part of the software engineering job. It is not necessarily the largest 

portion or the most costly. In fact, modern code generation tools exist to reduce design to code 

and test that code for validity, reliability, and dependability. Likewise, a number of types of 

process models provide repeatable, predictable processes or methodologies that improve 

productivity and quality. Some processes systematize or formalize the coding task. Others apply 

project management techniques to writing software. These types include representatives shown in 

XTable 4X. 

• Testing of parts of software, especially where code by two different engineers must work 

together, falls to the software engineer. This is not a point for diversity but does begin to address 

fault and system failures relative to diversity objectives and version independence. 

• Documentation represents an important (and often overlooked) task for formally recording the 

internal design of software for the purpose of future maintenance and enhancement. 

Documentation is most important for external interfaces, represents a first step for configuration 

management, and is not a potential point for diversity. 

• Software Training and Support is a step in which the user’s model of functionality first confronts 

the developer’s specification of that functionality. While an aspect of defense-in-depth, this is not 

a point for diversity among versions. Users will have lots of questions and software problems, 

which leads to the next phase of software development. 

• Maintaining and Enhancing software to cope with newly discovered problems or new 

requirements is not often viewed as a point for D3. It is a phase of software development where 

configuration management can have an effect on the safety envelop, with compounding 

consequences. While a small part of this phase is devoted to correcting faults, users and 

developers can infuse failure modes and complicate failure diversity among versions which have 

been subject to forced diversity in earlier phases. 
74 

Table 4. Software development process models

Process 

model name Examples or processes Notes 

Waterfall 

model 

• state requirements 

• requirement analyze 

• design a solution approach 

• architect a software framework for that 

solution 

• develop code 

• test (perhaps unit tests then system 

tests) 

• deploy 

• post implementation 

Oldest model. Steps finished sequentially. The 

process proceeds to the next step, just as builders 

don’t revise the foundation of a house after the 

framing has been erected. 

TIterative 

processesT 

 Prescribes the construction of initially small but 

ever larger portions of a software project to help 

all those involved to uncover important issues 

early before problems or faulty assumptions can 

lead to disaster. 

• Agile software development Agile processes use feedback, rather than 

planning, as their primary control mechanism. The 

feedback is driven by regular tests and releases of 

the evolving software. Agile processes seem to be 

more efficient than older methodologies, using less 

programmer time to produce more functional, 

higher quality software. Programmer as artist 

concept.

• Extreme programming Phases are carried out in extremely small (or 

“continuous”) steps compared to the older, “batch” 

processes. The (intentionally incomplete) first pass 

through the steps might take a day or a week, 

rather than the months or years of each complete 

step in the waterfall model. Relies upon specific 

design patterns and entity relationship diagrams. 

• Test driven development Requires that a unit test be written for a class 

before the class is written. Therefore, the class 

firstly has to be “discovered” and secondly defined 

in sufficient detail to allow the write-test-onceand-code-until-class-passes model that test-driven 

development actually uses. 

Formal 

methods • B-method 

• Petri nets 

• Rigorous Approach to Industrial 

Software Engineering (RAISE) 

• Vienna Development Method (VDM). 

• Specification notation example: 

Z notation 

---------------------------------------------------- 

Automata theory and finite state machines. 

Mathematical approaches to solving software (and 

hardware) problems at the requirements, 

specification, and design levels. 

---------------------------------------------------- 

Methodologies allow executable software 

specification and by-passing of conventional 

coding. 

Generic 

programming 

Algorithms are written in an extended 

grammar 

Grammar raises a nonvariable element or implicit 

construct in the base grammar to a variable or 

constant and allows generic code to be used, 

usually implementing common software patterns 

that are already expressible in the base language. 
75 

8.4 REGULATORY IMPACT OF SOFTWARE 

Software cannot typically be proven to be error-free and is therefore considered susceptible to CCFs 

if identical copies of the software are present in redundant channels of safety-related systems. At the 

heart of mitigating strategies to cope with CCFs is a judicious use of various diversity measures and 

an analysis of how each diversity measure can cope with particular categories of CCFs. 

NUREG/CR-6303 identifies the following six categories of diversity: 

• design diversity, 

• equipment diversity, 

• functional diversity, 

• human diversity, 

• signal diversity, and 

• software diversity. 

The role of software diversity in ensuring adequate defense against CCFs needs to be studied. In 

general, some of the unresolved issues in using D3 continue to be the following.X45 

1. How much D3 is adequate? 

2. What sets of diversity attributes can be used to identify adequate D3? 

3. Are there accepted best practices for approaching D3, and if so what are they? 

4. How much credit can be taken for built-in quality of a digital safety system? 

5. Are there standards that can be endorsed for use by applicants in the design and analysis of I&C 

systems for adequacy of the D3 approach? 

The use of diversity to protect against CCFs in software design is not likely to change. However, a 

great deal of effort can go toward advanced software development techniques that reduce the 

likelihood of software faults in a digital safety function, make the software less costly, and make the 

software easier to review and license for use. The conventional tools of the software design 

methodology using the waterfall model have been universally adopted in nuclear software 

development. The process is cost intensive and relies to a large extent on human involvement at each 

step of the waterfall to inspect and test results and to verify and validate that the requirements have 

been met. The goal of high integrity software developments is to improve the process by automating 

and systematizing the methods. The range of advanced software techniques that are being developed 

include methods that automate design steps and report generation, organize the work in new ways that 

tend to make errors less likely, or automate testing and V&V. It is no longer just the computer 

program that runs on the device that affects quality, but the much larger system of software used to 

develop it. The challenge for regulatory bodies is to find ways to review and accept the new strategies 

using complex, automated design and development tools. In this regard, PRAXIS, a British company, 

claims to have developed a highly reliable and UprovableU code based on a National Security Agency 

funded project.TPD

138DPT The software has approximately 10,000 lines of code. 
This Page Intentionally Left Blank 
77 

9. INSTRUMENTATION AND CONTROLS ARCHITECTURES IN NEW PLANTS 

9.1 TRENDS IN DIGITAL ARCHITECTURES IN NUCLEAR POWER PLANTS 

Digital I&C architectures are deployed in several international reactors such as Chooz B France, 

Sizewell B (United Kingdom), Darlington (Canada), Lungmen ABWR (Taiwan), Temeline (Czech 

Republic), DukovaNy (Czech Republic), and the EPR. A review of I&C features of several of these 

reactor designs indicates fully-digital and network communication architectures, with analog trip 

backup in some cases. While the primary focus of digital communication in the nonnuclear and other 

non-safety-critical environments is toward ever increasing bandwidth, the focus of nuclear I&C 

digital communication issues is (a) electrical and functional independence between safety and 

non-safety divisions, (b) deterministic communication among safety systems and assurance of 

fail-safe communication, and (c) assurance that CCF in the communications systems cannot 

compromise the function of the safety systems. 

Three new designs—the US-EPR, the U.S. version of the EPR, by AREVA NP; the APWR by MHI; 

and the ESBWR by General Electric-Hitachi (GEH)—are briefly described here to illustrate the 

current state in digital I&C architectures in NPPs. 

9.2 EUROPEAN PRESSURIZED REACTOR 

EPR (the U.S. version is called the Evolutionary Pressurized Reactor or US-EPR) is designed by 

Framatome ANP, an AREVA and Siemens company, and is representative of the latest in PWR I&C 

advancement. There are three variants of the EPR design, which are either under construction [e.g., 

Olkiluoto- (OL-) 3 in Finland and Flamanville- (FL-) 3 in France] or undergoing design certification 

[e.g., US-EPR]. XTable 5X summarizes the differences among the three EPR I&C variants. 

Table 5. Differences in instrumentation and controls among the different 

European/Evolutionary Pressurized Reactor designs 

System Olkiluoto-3 

(Finland) 

Flamanville-3 

(France) United States 

Protection system (PS) TXS TXS TXS 

Safety automation system (SAS) TXP TXP TXS 

Reactor control, surveillance, and 

limitation system (RCSL) 

TXS TXS TXS 

Process automation system (PAS) TXP TXP TXP 

Priority actuation and control 

system (PACS) 

TXS (priority 

modules) 

Switchgear cabinets TXS (priority 

modules) 

Safety information and control 

system (SICS) 

Mostly conventional 

I&C, limited QDS 

Mostly QDS, limited 

conventional I&C 

Mostly QDS, limited 

conventional I&C 

Process information and control 

system (PICS) 

TXP TXP TXP 

Severe accidents automation 

system 

TXS No information 

available 

TXS 

Diverse protection functions TXP/HBS TXP TXP 

Legend: TXS—TELEPERM XS; TXP—TELEPERM XP; QDS—qualified display system; HBS—hardwired backup 

system. 

9.2.1 System-Level Instrumentation and Controls Architecture 

The EPR I&C architecture can be considered on three levels: 
78 

• Level 0, process interface level; 

• Level 1, system automation level; and 

• Level 2, unit supervision and control level. 

Level 0 systems, (i.e., process interface level) form the physical interface between Level 1 

subsystems and sensors, actuators, and switchgear. Level 1 systems (i.e., system automation level) 

consist of the protection system (PS), safety automation system (SAS), process automation system 

(PAS), priority actuation and control system (PACS), and reactor control, surveillance, and limitation 

(RCSL) system. Level 2 systems consist of the workstations and panels of the MCR, remote 

shutdown station (RSS), technical support center (TSC), process information and control system 

(PICS) and safety information and control system (SICS). 

Each level may contain both safety-related and non-safety-related systems. XFigure 27X is a block 

diagram illustrating the main I&C systems and subsystems of the EPR. These systems and 

subsystems are also listed in the first column of XTable 5X. In this configuration, all functions necessary 

to provide a safe shutdown state are either automatically generated in the SAS or manually initiated 

and processed by the PICS and SAS.TPD

139DPT 

Figure 27. U.S. Evolutionary Pressurized Reactor instrumentation and controls architecture. 

All I&C functions and equipment are categorized as safety related, quality related, and 

non-safety-related according to their importance to safety. All safety-related components are 

implemented on Class 1E equipment. Higher-classified functions have priority over commands from 

Safety I&C Operational I&C 

Safety connections Operational connections 

QDS: Qualified display CNV I&C: Conventional I&C 

Level 1 Communication

Level 2 Communication 

PACS 

PLANT EQUIPMENT (SENSORS AND ACTUATORS)

PICS 

Computers 

PLANT 

DISPLAY 

PICS 

TECHNICAL SUPPORT 

CENTER (TSC) 

I&C SERVICE 

CENTER (ISC) 

I&C ENGINEERING 

WORKSTATIONS 

REMOTE SHUTDOWN STATION (RSS) 

QDS 

CNV 

I&C 

SICS PICS 

PLANT 

DISPLAY 

MAIN CONTROL ROOM 

(MCR) 

PICS

PLANT 

DISPLAY 

PLANT 

DISPLAY 

SICS

QDS QDS 

CNV 

I&C

CNV 

I&C 

PS SAS RCSL PAS 

Level 2 (Unit 

Supervision 

And Control)

Level 1 

(System 

Automation) 

Level 0 

(Process Level) 
79 

lower-classified functions [i.e., (1) Class 1E has priority over (2) quality-related class, which has 

priority over (3) non-safety-related class]. 

9.2.1.1 Safety-Related Systems 

The following I&C systems of the EPR are safety-related: 

• PACS, 

• PS, 

• SAS, and 

• SICS. 

Priority Actuation and Control System 

PACS monitors and controls both safety-related and non-safety-related actuators. Each actuator is 

controlled by a separate PACS module, as shown in XFigure 28X. Each PACS module has to fulfill the 

high-availability and reliability requirements against CCFs. To control an actuator, the corresponding 

PACS module receives and processes all commands. When an actuation request is issued, the PACS 

responds by processing the request according to command priority encoded into the logic circuitry of 

the module. As a result, a command output is generated and sent to the actuator. 

Figure 28. Block diagram of Olkiluoto-3 Priority and Actuation 

Control System (PACS) module. 

The PACS input signals can include status and health monitors for the actuator it controls. Depending 

on the current operational situation, contradictory commands may be given by different I&C 

subsystems to particular actuators. Consequently, prioritization rules have been established and 

encoded into each PACS module to resolve any conflicting commands in a manner allowing the unit 

to respond only to the highest priority command. Each PACS module has two major components as 

shown in XFigure 28X. The first component is a programmable logic device consisting of interconnected 

logic gate arrays. The second is a PROFIBUS controller in the form of an ASIC. The PROFIBUS 
80 

controller provides the communication interface to the TXS of the PS, the RCSL system, the Severe 

Accidents Automation System, or the TELEPERM XP (TXP) of the SAS. 

Protection System 

Implemented in the TXS platform, the PS is the main I&C line of defense. The primary function of 

the PS is to bring the plant to a controlled state if a design basis event occurs. Tripping the reactor, 

actuating containment isolation, actuating Emergency Core Cooling System (ECCS), initiating 

Anticipated Transient Without Scram (ATWS) mitigating actions, and performing Emergency 

Feedwater (EFW) system protection and control are some of the actions covered by the PS. The PS 

reactor trip function uses voting logic to screen out potential upstream failures of sensors or 

processing units. 

The PS is a digital system located in dedicated cabinets in the nuclear island. The system is 

implemented in four divisionally separate trains, each with its own Class 1E power source. 

Additionally, each PS cabinet is provided with its redundant power supplies for the electronics. The 

PS is made functionally independent of all other I&C systems. Connections with other I&C systems 

are implemented through isolated channels. The PS can perform its own internal self-diagnostics 

functions and alert the operators to unusual conditions or internal failures. 

Safety Automation System 

The SAS is a digital I&C system dedicated to automatic and manual control and measuring and 

monitoring functions needed to bring the plant to a safe shutdown state. The SAS is also implemented 

in TXS platform. It receives process data from plant instrumentation and switchgear, sends actuation 

signals either directly or via PACS, and sends monitoring signals to the SICS and PICS. 

The SAS functions include post-accident automatic and manual control, the monitoring functions 

needed to bring the plant to the safe shutdown state, and automatic initiation of I&C functions to 

prevent spurious actuations that could result in design basis accidents. 

Safety Information and Control System 

The main purpose of the SICS is to control certain safety-related support systems, such as the 

component cooling water system (CCWS) and ventilation, in the event that the PICS becomes 

unavailable. The SICS can be used to monitor and control the plant for a limited time in steady-state 

power operation. 

The SICS consists of a small inventory of conventional (continuously visible) HSIs and a series of 

qualified display systems (QDSs). The QDSs are safety-related and are therefore required to be 

qualified to Finnish Class SC-2 (U.S. Class 1E) standards. Non-safety-related information can be 

displayed on the SICS. Any non-safety-related data displayed on SICS is processed by a 

safety-related Class 1E computer before being sent to the SICS display; therefore, there is no 

commingling of safety and nonsafety software on the SICS display system. During normal operation, 

the SICS controls are deactivated to reduce the risk of spurious actuations due to any possible hazards 

or internal equipment failures. 

9.2.1.2 Non-Safety-Related Systems 

The following I&C systems of the EPR are non-safety-related: 

• PAS, 

• RCSL system, and 

• PICS. 
81 

Process Automation System 

The PAS controls non-safety-related systems and also contains some backup functions for reactor trip 

and actuation of engineered safety features (ESF) that are implemented using diverse hardware and 

software from the primary reactor trip and Engineered Safety Features Actuation Systems (ESFASs). 

The PAS is implemented with the TXS platform. 

Reactor Control, Surveillance, and Limitation System 

The RCSL system provides automatic, manual, and monitoring functions to control and limit the 

main reactor and nuclear steam supply system (NSSS) parameters. When these parameters deviate 

from the desired operational values, before the parameters reach trip set points, the RCSL system 

would take effect. This action by the RCSL system tends to reduce reactor trips and PS challenges. 

For example, the RCSL is designed to take actions such as runback of power if the plant operational 

parameters exceed their operational boundaries to prevent challenging the PS. The RCSL is also 

implemented in the TXS platform. 

Process Information and Control System 

The PICS is used to monitor and control the plant under any plant conditions. Implemented in the 

TXP platform, the PICS uses computers, VDUs, and soft controls. It has access to all Level 1 

systems. Components of the PICS include the following. 

• Displays for monitoring and control at the operator workstations in the MCR and at the shift 

supervisor’s location. 

• Large screen or projected video display for the plant overview display in the MCR. 

• Displays for monitoring and control in the RSS. 

• Displays for monitoring in the TSC. 

• Printing stations and information recording/archiving stations. 

The PICS displays alarms in the event of abnormalities in processes or systems and provides guidance 

to the operators in performing the appropriate corrective actions. 

9.2.1.3 Communication Systems 

Each I&C system manages its own internal exchanges (including data exchange between divisions) 

without using external resources. Data exchange between the different I&C systems is performed 

primarily through standard exchange units connected to the corresponding system networks.TPF

*

FPT

,

TD

140DTP

(Note that OL-3 uses two-way communication between PICS and PS/SAS.) 

Mode of Sensor Signal Transmission and Shared Sensor Implementation 

Most sensors use 4–20 mA (or in some cases 0–5 V) analog transmission. There is no sharing of 

sensors between functionally diverse subsystems (e.g., between sensors on subsystem A and sensors 

on subsystem B).TPD

141DPT However, partial trip data are shared between divisions for voting rights. Sensor 

signals are also shared for the purpose of signal validation. 

Safety System Interfaces 

The monitoring and service interface (MSI) module forms the boundary and interface between the 

safety system and the safety panel located in the CR, as shown in XFigure 29X (MSI is not shown in 

 

TP

*

PTThis information primaTrily pertains to the U.S. Evolutionary Pressurized Reactor (US-EPR). While specific information on 

communication methodology for the Olkiluoto-3 (OL-3) could not be obtained, the instrumentation and controls 

architecture and communication methods for the OL-3 and US-EPR are similTar. 
82 

XFigure 27X and XFigure 28X). The MSI module, which is classified as Class 1E (Finnish Class SC-2), 

also serves as a safety-related logical barrier between the rest of the safety system and the nonsafety 

interfaces. The MSI module is designed to ensure that only predefined messages are transferred 

between the safety system and non-safety-related displays; it is not responsible, however, for plant 

control functions. 

Communication via the maintenance panel (service unit) to a safety channel can be performed only 

after that channel has been turned off via a key switch. For OL-3, the TXS equipment (i.e., the four 

divisions of the PS) is located in the four safeguards buildings.TPF

*

F The processor key switches are PT

located in the equipment cabinets.TPF

†

F Maintenance data are written to the MSI module in a separate PT

memory area. 

Figure 29. The monitoring and service interface (MSI) module forms a logical 

boundary between the rest of the safety system and the nonsafety interfaces. 

The MSI module is in continuous communication with the safety divisions to receive status and 

diagnostic information. This information includes continuous checks for sensor deviation (the auto 

channel check feature). Many precautions are taken to prevent access through the MSI module from 

affecting the safety function. These precautions include strict access control features and predefined 

connection/messaging protocols. In addition, the MSI module confirms the identity and bypass status 

of a safety division to ensure that maintenance access is enabled only for one division at a time and 

when that division is in bypass. However, once access to a safety division is granted through the MSI 

module, it is possible to alter the parameters of the safety application’s logic blocks. The MSI module 

also provides a connection to plant computers, but it is a one-way uplink. 

9.2.1.4 Human-System Interface System 

The HSI system has four interface units: (1) MCR, (2) RSS, (3) local control stations, and (4) TSC. 

During normal operating conditions, the plant is supervised and controlled from the MCR. The MCR 

is equipped with essentially identical operator workstations consisting of PICS-driven screens (i.e., 

 

TP

*

PTThis is also true for the US-EPR. 

TP

†

PTThe TELEPERM XS equipment cabinets are located in the control room for Oconee. 
83 

VDUs) and soft controls. The MCR also includes the following additional monitoring and control 

equipment . 

• The plant overview panel consisting of several large PICS-driven screens that provide overviews 

of plant status and main parameters. 

• The safety control area with the SICS displays and controls available as backup in case of 

unavailability of PICS. 

• Fire detection and fire fighting controls and site closed circuit TV monitoring screens. 

If the MCR becomes inaccessible, the operators can supervise and control the plant from the RSS. 

The RSS is equipped with the following. 

• Manually-actuated switches for disconnecting all the MCR equipment that may generate 

component actuation of the Level 1 systems and placing the RSS workstations in the control 

mode. Technical and administrative precautions prevent spurious or unauthorized actuation of 

this function. 

• Two operator workstations consisting of PICS-driven screens (VDUs) and soft controls that are 

of the same type and provide the same functionality as those in the MCR. The operators can bring 

the plant to safe shutdown state and monitor plant conditions from these operator workstations. 

• Communication equipment for maintaining communications with other plant personnel. 

The TSC is used by the technical support team in the event of an accident. The additional staff in the 

TSC analyzes the plant conditions and supports post-accident management. The TSC is equipped 

with PICS screens that have access to plant information. No process control function is available in 

the TSC. Appropriate communications equipment is also provided in the TSC. 

9.2.1.5 Plant-Specific Systems 

Hardwired Backup Systems 

The OL-3 design incorporates an automatic hardwired backup system (HBS). The HBS contains a 

small subset of the PS functions. They include automatic actions needed to cope with certain design 

basis events. The HBS uses FPGA technology. The FPGA is not programmable while installed, and it 

is considered sufficiently diverse from the other major platforms. In addition to the automatic HBS, a 

manual HBS is also provided. 

Design Features to Reduce the Probability of Unintended Behaviors and/or Latent Faults in the 

Safety Systems 

The I&C design features include (1) deterministic processing; (2) asynchronous operation of each 

computer—extensive self-monitoring; (3) signal validation techniques; (4) voting techniques; 

(5) inherent and engineered fault accommodation techniques; (6) software life cycle, including V&V; 

(7) operating experience with standard library of application software function locks; and 

(8) communication independence measures. 

9.2.2 Instrumentation and Controls Architecture Platforms 

In the US-EPR, many subsystems within overall I&C systems are implemented with either the TXS 

or TXP platform, with some exceptions of hardwired implementations. A brief synopsis of the two 

platforms is presented below. 
84 

9.2.2.1 TELEPERM XS Platform 

The basic building blocks of the TXS system architecture can be grouped into the following 

categories. 

1. System hardware: The TXS selected hardware platform uses a processing computer module that 

includes RAM for the execution of programs, flash EEPROM for storing program code, and 

EEPROM for storing application program data. 

2. System software: The TXS consists of a set of quality-controlled software components. The 

execution of the software centers on the operating software system that was developed by 

Siemens specifically for the TXS system. The operating system communicates with the platform 

software and application software. The platform software includes the runtime environment 

program that provides a unified environment for execution of the function diagram modules. 

3. Application software: The application software performs plant-specific TXS safety-related 

functions using function block modules, which are grouped into function diagram modules. The 

application software is generated by specification and coding environment tools that use qualified 

software modules from a function block library to construct a specific application. 

The following are important TXS software features. 

• Strictly cyclic processing of application software—the system processes data asynchronously 

(i.e., there is no real-time clock with which redundant processors can synchronize). 

• No dynamic memory allocation—each variable in the application program has a permanent 

dedicated location in memory. This prevents memory conflicts typically caused by dynamic 

memory allocation. 

• No process-driven interrupts. 

9.2.2.2 TELEPERM XP Platform 

The TXP comprises the following subsystems. 

• The AS 620 automation system. 

• The OM 650 process control and management system. 

• The ES 680 engineering system. 

• The CT 675 commissioning tool. 

• The DS 670 diagnostic system. 

• The SIMATIC NET industrial Ethernet bus system. 

The AS 620 carries out tasks of the group and individual control levels. It collects measured values 

and status from the process, carries out open- and closed-loop control functions, and passes the 

resulting commands onto the process. 

The OM 650 is an HSI system. 

The ES 680 is an integral system for the configuration of subsystems. It is used to configure the plantspecific automation, process control, and process information software functions. 

The CT 675 performs commissioning and maintenance tasks. 

The DS 670 allows detailed system status evaluation and system analysis through informational 

diagnostics functions. The diagnostics station provides all I&C fault alarms including information on 

the faulty components. 
85 

The SIMATIC NET is a fast LAN industrial Ethernet bus system. 

Communication between the I&C system components and the AS 620, OM 650, ES 680 and DS 670 

systems is carried out via the plant bus. 

9.3 ADVANCED PRESSURIZED WATER REACTOR 

APWR is designed and manufactured by MHI. The U.S. version, called US-APWR, is an 

evolutionary 1,700-MWe PWR. The design uses high-performance steam generators, a neutron 

reflector around the core to improve fuel efficiency, redundant core cooling systems and refueling 

water storage inside the containment building, and a fully-digital I&C system. 

9.3.1 System-Level Instrumentation and Controls Architecture 

The system-level I&C architecture for the APWR is shown in XFigure 30X and consists of the following 

four levels: 

1. protection and safety monitoring system (PSMS), 

2. plant control and monitoring system (PCMS), 

3. HSI system, and 

4. diverse actuation system (DAS). 

Each level may contain multiple safety- and non-safety-related subsystems or components. 

PSMS provides automatic reactor trip via the reactor protection system (RPS) and ESFAS. The safety 

logic system (SLS) performs the component-level control logic for safety actuators in all trains based 

on the ESFAS signals (e.g., motor-operated valves, solenoid-operated valves, and switchgear). 

The non-safety-related PCMS provides automatic controls for normal operation. The safety-related 

PSMS provides automatic reactor trip and ESF actuation. These same safety and nonsafety functions 

may be manually initiated and monitored by operators using the HSI system, which includes both 

safety-related and non-safety-related sections. The HSI system is also used to manually initiate other 

safety and nonsafety functions that do not require time-critical actuation, including safety functions 

credited for safe shutdown of the reactor. After manual initiation from the HSI system, all safety 

functions are executed by the PSMS, and all nonsafety functions are executed by the PCMS. The HSI 

system also provides all plant information to operators, including critical parameters required for 

post-accident conditions. 

The PSMS and the PCMS use the Mitsubishi Electric Total Advanced Controller (MELTAC) digital 

platform.TPF

*

FPT 

The DAS is classified as a nonsafety system that provides monitoring of key safety parameters and 

backup automatic and manual actuation of the safety and nonsafety components required to mitigate 

anticipated operational occurrences and accidents. The DAS consists of hardwired analog 

components. Thus, a postulated CCF in the software in the digital protection or control systems (i.e., 

PSMS and PCMS) will not impair the DAS function. 

 

TP

*

PTThe MELTAC platform is applied to the protection and safety monitoring system, which includes the reactor protection 

system, engineered safety features actuation system, safety logic system, and safety-grade human-system interface. In 

addition, the MELTAC platform is applied to non-safety systems such as the plant control and monitoring system. The 

MELTAC equipment applied for non-safety applications is the same design as the equipment for safety applications. 

However, there are differences in quality assurance methods for software design and other software life-cycle processes. 
86 

Figure 30. Overall architecture of the Advanced Pressurized-Water Reactor 

instrumentation and controls system.X

145X

A brief description of these systems is provided below. Detailed descriptions can be found in 

references D142D–DDDDD145D. 

9.3.1.1 Safety-Related Systems 

Safety-related I&C systems on US-APWR are implemented on a fully-digital MELTAC platform. 

Safety-related I&C systems are 

• RPS, 

• ESFAS, 

• SLS, 

• safety-grade HSI system, and 

• conventional switches (train-level manual actuation). 

All safety-related systems are four-train redundant. A brief description of each system is given below. 

The HSI system will be described in a dedicated subsection. 

Reactor Protection System 

Each train performs two-out-of-four voting logic for like sensor coincidence to actuate trip signals to 

the four trains of the reactor trip breakers and actuate ESF signals to the four trains of the ESFAS. 

The RPS consists of four redundant trains, with each train located in a separate I&C equipment room. 

The logic functions within the RPS are limited to bi-stable calculations and voting for reactor trip and 
87 

ESF actuation. Each train also includes a hardwired manual switch on the operator console to directly 

actuate the reactor trip breakers. This switch bypasses the RPS digital controller. 

The system includes failed equipment bypass functions and microprocessor self-diagnostics, 

including data communications and features to allow manual periodic testing of functions that are not 

automatically tested by the self-diagnostics, such as actuation of reactor trip breakers. Manual 

periodic tests can be conducted with the plant online and without jeopardy of spurious trips due to 

single failures during testing. 

Engineered Safety Features Actuation System 

For the US-APWR, there are four ESFAS trains. Each ESFAS train receives the output of the ESF 

actuation signals from all four trains of the RPS. 

The system-level ESF actuation signal from each of the four RPS trains is transmitted over isolated 

data links to an ESFAS controller in each of the ESFAS trains. Whether automatically or manually 

initiated, train-level ESF actuation signals are transmitted from both subsystems of the ESFAS 

controller to the corresponding train of the SLS. 

Each ESFAS controller consists of a duplex architecture using dual CPUs. Two-out-of-four voting 

logic for like system-level coincidence is performed twice within each train through the redundant 

subsystems within each ESFAS controller to automatically actuate train-level ESF actuation signals 

for its respective train of the SLS. Each subsystem generates a train-level ESF actuation signal if the 

required coincidence of system-level ESFAS actuation signals exists at its input and the correct 

combination of system-level actuation signals exists to satisfy logic sensitive to specific accident 

situations. 

The ESF system is a fully microprocessor-based system, and each microprocessor performs 

self-diagnostics, including data communications. The system also includes features to allow manual 

periodic testing of functions that are not automatically tested by self-diagnostics, such as manual 

system-level actuation inputs. Manual periodic tests can be conducted with the plant online and 

without jeopardy of spurious system-level actuation due to single failures during testing. 

Safety Logic System 

The SLS is a microprocessor-based system that has redundancy within each train and microprocessor 

self-diagnostics, including data communications. The system also includes features to allow periodic 

testing of functions that are not automatically tested by the self-diagnostics, such as final actuation of 

safety components. The SLS is designed to perform the component-level control logic for safety 

actuators in all trains based on ESF actuation signals (e.g., motor-operated valves, solenoid-operated 

valves, and switchgear). Manual periodic tests can be conducted with the plant online and without 

jeopardy of spurious system-level actuation due to single failures during testing. 

The SLS has one train for each plant process train. Each train of the SLS receives ESF system-level 

actuation demand signals and LOOP load-sequencing signals from its respective train of the ESF 

actuation system. The SLS also receives manual component-level control signals from the operator 

console and remote shutdown console (safety VDUs and operational VDUs) and manual 

component-level control signals from the hardwired backup switches on the diverse HSI panel. It also 

receives process signals from the RPS for interlocks and controls of plant process systems. This 

system performs the component-level control logic for safety actuators (e.g., motor-operated valves, 

solenoid-operated valves, and switchgear). 
88 

The SLS controllers for each train are located in separate I&C equipment rooms. The system has 

conventional I/O portions and I/O portions with priority logic to accommodate signals from the DAS. 

9.3.1.2 Non-Safety-Related Systems 

Plant Control and Monitoring System 

The PCMS encompasses all non-safety-related I&C systems in the plant with the exception of special 

purpose controllers (e.g., alternate generator engine controls). The PCMS interfaces with these other 

non-safety-related systems and components so there is only one fully integrated HSI system in the 

MCR. 

One of the major systems within the PCMS is the reactor control system. The reactor control system 

receives nonsafety field sensor signals. This system also receives status signals from plant process 

components and manual operation signals from the operator console to control and monitor the NSSS 

process components. This system controls continuous control components such as air-operated valves 

and discrete state components such as motor-operated valves, solenoid-operated valves, pumps, etc. 

The PCMS is a microprocessor-based system that is intended to achieve high reliability through 

segmentation of process system groups (e.g., pressurizer pressure control, feedwater control, rod 

control); redundancy within each segment; and microprocessor self-diagnostics, including data 

communications. 

Diverse Actuation System 

The DAS is implemented as a redundant analog system. The DAS shares sensor inputs with the 

PSMS through analog interfaces that are not subject to the postulated CCF in the PSMS. Interfaces to 

safety process inputs and the SLS outputs are isolated within the safety systems through qualified 

conventional isolators. 

9.3.1.3 Communication Systems 

The data communication system (DCS) consists of the plant-wide unit bus, safety bus for each PSMS 

train, maintenance network for each PSMS train, and the PCMS (five maintenance networks total). 

The DCS also contains data links for point-to-point communication and an I/O bus for each 

controller. This includes information and controls for the MCR, RSR and TSC (only monitoring). The 

DCS interfaces with the station bus, which is an information technology network (i.e., not I&C). The 

station bus provides information to plant personnel and to the emergency operations facility (EOF). 

The major components of the DCS within the overall I&C architecture can be seen in XFigure 30X, and 

the DCS interfaces to the HSI system and the unit bus are shown in XFigure 31X. 

Although the DCS is a distributed and highly interconnected system, there is communication 

independence to prevent electrical and communication processing faults in one division (safety or 

nonsafety) from adversely affecting the performance of safety functions in other divisions. To prevent 

electrical faults from transferring between divisions and between different plant fire areas for the 

MCR, RSR, and I&C rooms, qualified fiber-optic isolators are used. Communication faults are 

prevented through data integrity verification. 
89 

Figure 31. Communication network between the human-system interface system and other systems. 

US-APWR uses asynchronous communications (i.e., controller performs no communication 

“handshaking” that could disrupt deterministic logic processing). Deterministic communication is 

ensured by using predefined data size and structure. Communication channels are independent (i.e., 

electrical or communication faults in one electrical division cannot adversely affect performance of 

the safety function in other divisions). 

Hardwired interlocks in the controller or safety VDU processor ensure changes to software cannot be 

made through the data communication interface while the controller or safety VDU processor is 

operating. 

Mode of Sensor Signal Transmission and Shared Sensor Implementation 

Redundant divisions of the RPS are physically and electrically isolated from the nonsafety control 

systems. Where safety sensors are shared between control and protection systems, signal selection 

logic in the control system prevents erroneous control actions from single sensor failures. Eliminating 

these erroneous control actions prevents challenges to the RPS if it is degraded because of the same 

sensor failure. Where nonsafety signals control safety systems or components, logic in the safety 

systems ensures prioritization of safety functions. 

For each design basis accident addressed in the plant safety analysis, two diverse parameters are used 

to detect the event and initiate the protective actions. These diverse parameters are processed in two 

separate controller groups within each train of the RPS. 

Safety-related Human-System Interface System X 

(HSIS) 

Non-safety-related Human-System Interface System 

(HSIS) 

E/O E/O H/W E/O H/W

Reactor Protection 

System X 

(RPS) 

Diverse 

Actuation System

(DAS) 

Train X N

Train X

Train X N

Safety Logic 

System X 

(SLS) 

Reactor Trip 

Breaker X 

(RTB) 

ESF 

Actuation System X 

(ESFAS) 

H/W E/O E/O E/O E/O H/W

Train X 

Train X

Train X

Train X

Train X

Train X N

E/O E/O

N

E/O E/O

N N

Reactor 

Control 

System 

Other 

Control 

Systems 

E/O E/O

N N

a c b c b a d e f g f g

b c a e h 

Unit Bus 

Data Link 

Hardwired 

E/O E/O Converter

H/W Hardwired Device

Train X Train X Signal 

N Non-safety Signal
90 

The two diverse parameters are monitored by two separate sensors that interface to two separate 

digital controllers within the RPS. Each of the two controllers processes these inputs to generate 

reactor trip and/or ESF actuation signals. This two-fold diversity is duplicated in each redundant RPS 

train. The processing of diverse parameters results in functional redundancy within each RPS train. 

This functional redundancy helps minimize potential CCFs. 

Safety System Interfaces 

To ensure there is no potential for the nonsafety system to adversely affect any safety functions, the 

interface between the nonsafety operational VDUs in the PCMS and the PSMS is isolated as 

described below. 

• Electrical independence: Fiber optic interfaces between the PSMS and PCMS prevent 

propagation of electrical faults between divisions. 

• Data processing independence: The PSMS uses communication processors for the PCMS that are 

separate from the processors that perform safety logic functions. The safety processors and 

communication processors communicate via dual ported memory. This ensures there is no 

potential for communications functions, such as handshaking, to disrupt deterministic safety 

function processing. 

• No ability to transfer unpredicted data: There is no file transfer capability in the PSMS. Only 

predefined communication data sets are used between the PSMS and PCMS. Therefore any 

unknown data are rejected by the PSMS. 

• No ability to alter safety software: The software in the PSMS cannot be changed through the 

nonsafety communication network. The PSMS software is changeable only through the 

maintenance network, which is key locked and alarmed. 

• Additional protection against cyber threats: The PCMS and PSMS will be controlled under the 

most stringent administrative controls for cyber security. There is only one-way communication 

to other systems that are not under these same controls. 

• Acceptable safety function performance: Manual controls from the safety VDU can have priority 

over any nonsafety controls from the PCMS. 

• Failures of Nonsafety Systems Are Bounded by the Safety Analysis: Any plant condition created 

by the worst-case erroneous/spurious nonsafety data set (e.g., nonsafety failure commanding 

spurious opening of a safety relief valve) is bounded by the plant safety analysis. 

The operational VDUs and associated processors are not Class 1E; however, they are tested to the 

same seismic levels as the PSMS. During testing, the operational VDUs and associated processors 

have demonstrated ability to maintain physical integrity and all functionality during and after an 

operating basis earthquake and a safe shutdown earthquake. 

9.3.1.4 Human-System Interface Systems 

The complete HSI system includes portions of the safety-related PSMS and the non-safety-related 

PCMS and the non-safety-related DAS. The major components of the HSI system include the 

operator, shift technical advisor, and supervisor consoles; large display panel and adverse HSI panel; 

and various VDU processors. Plant information and controls (i.e., for all safety and nonsafety 

divisions) are displayed and accessed on the nonsafety operational VDU screens of the operator 
91 

console. All operations from the operator console are available using touch screens or other pointing 

devices on the nonsafety operational VDUs. Safety VDUs on the operator console provide access to 

safety information and controls using touch screens. One or more safety VDUs has been allocated for 

each safety train. 

Safety-Grade Human-System Interface System 

The safety-grade HSI system consists of conventional hardwired switches for manual actuation of 

reactor trip and ESF actuation signals, and safety VDUs and processors, which provide post-accident 

monitoring indications and manual controls and status indications for all components in safety-related 

process systems. 

Each train of the safety-grade HSI system interfaces with the corresponding trains of all other systems 

within the PSMS. There are safety-grade HSI components for each train located on the operator 

console and the remote shutdown console. The safety VDUs and switches for each train are isolated 

from each other. The safety VDUs and switches at the operator console and the remote shutdown 

console are also isolated from each other and from the controllers in the PSMS to ensure that HSI 

failures that may result from a fire in one location cannot adversely affect the HSI in the alternate 

location. 

9.3.1.5 Plant-Specific Systems 

I&C Design Features to Reduce the Probability of Unintended Behaviors and/or Latent Faults in 

Safety Systems 

This equipment includes automated testing with a high degree of coverage and additional overlapping 

manual test features for the areas that are not covered by automated tests. Most manual tests may be 

conducted with the plant online and with the equipment bypassed or out of service. Equipment that 

cannot be tested with the plant online can be tested with the plant shutdown. Depending on the system 

design for a specific plant, the equipment is configured with N or N+1 redundancy, where N is the 

number of divisions needed for single failure compliance. For systems with N+1 redundancy, the 

single failure criterion is met with one division bypassed or out of service. The redundancy 

configuration for each plant system is described in other digital system licensing documentation. 

9.3.2 Instrumentation and Controls Architecture Platforms 

9.3.2.1 Mitsubishi Electric Total Advanced Controller Platform (MELTAC) 

The MELTAC platform is based on using qualified building blocks that can be used for all safety 

system applications. The building blocks are the following items. 

• Controller 

• Safety VDU panel 

• Safety VDU processor 

• Control network 

• Data link 

• Engineering tool 

• Maintenance network 
92 

Figure 32. Typical configuration of the Mitsubishi 

Electric Total Advanced Controller platform. 

System Hardware 

The controller for the MELTAC platform consists of one CPU chassis including one or two 

subsystems, one switch panel, and one fan unit. Each subsystem consists of a power supply module, 

CPU modules, control network I/F module, system management module, and two bus master 

modules. Each subsystem communicates with the control network via its own optical switch. The 

controller for the MELTAC platform also consists of multiple Ι/Ο chassis each with multiple I/O 

modules. 

The CPU module uses a 32-bit microprocessor with enhanced speed due to the high-speed SRAM and 

cache. This processor module is IEEE standard Futurebus+ compliant and performs internal 

operations and data transmission with modules such as the bus master module and control network 

interface module via Futurebus+. 

This module uses ultraviolet-erasable PROM for storing the basic software and flash EEPROM for 

storing the application software such as logic symbol interconnections, set points, and constants. 

System Software 

To achieve deterministic processing, the basic software of the MELTAC platform adheres to the 

following design principles: 

• There is only single task processing. 

• Interrupts are not used for any processing other than error processing. 

Console Controller 

(Other Division) Controller

Controller Safety VDU 

Processor 

Controller Controller Engineering 

Tool 

Safety VDU Panel 

Control Network 

Data Link 

Maintenance Network 
93 

Application Software 

Application software for functional algorithms is designed by combining simple graphical logic 

symbols such as AND, OR, and NOT. The application software graphical block diagram is 

automatically converted into execution data that are executed directly by the operation process of the 

basic software. The operation process of the basic software executes the functional symbol software 

sequentially according to the execution data. Application software execution data are stored in the 

flash EEPROM of the CPU module. 

The MELTAC platform is capable of taking three different kinds of configuration. 

• Single Controller Configuration: The controller includes one subsystem. The subsystem operates 

in control mode (Control mode means the subsystem controls the outputs to plant components.). 

• Redundant Parallel Controller Configuration: The controller includes two subsystems, each of 

which operates in control mode. 

• Redundant Standby Controller Configuration: The controller includes two subsystems. One 

subsystem operates in control mode while the other subsystem operates in standby mode. 

(Standby mode means the subsystem is closely monitoring the operation of the subsystem in 

control mode, including memory states. If that subsystem fails, the subsystem operating in 

standby mode will automatically switch to control mode with no bump in the control outputs.) 

Any of the three configurations may be applied to safety systems; the configuration is determined 

based on the application system requirements. 

9.4 ECONOMIC SIMPLIFIED BOILING WATER REACTOR 

Designed by GEH Nuclear Energy, the ESBWR is a 1,500 MWe natural circulation BWR that 

incorporates passive safety features. The design is based on its predecessor, the 670 MWe Simplified 

Boiling Water Reactor, and uses certain features of the certified ABWR. Natural circulation is 

enhanced by using a taller vessel and a shorter core and by reducing the flow restrictions. Highpressure water level control and decay heat removal during isolated conditions are accomplished by a 

unique design feature called isolation condenser system (ICS). After the automatic depressurization 

system starts, a gravity-driven cooling system (GDCS) provides low-pressure water level control. 

Containment cooling is provided by a passive system. 

More information on the ESBWR can be found in references D146D–DDDDD149D.

9.4.1 System-Level Instrumentation and Controls Architecture 

The I&C system for the ESBWR is a distributed control and information system (DCIS). The 

ESBWR DCIS is an arrangement of I&C networked components and individual systems that provide 

processing and logic capability, remote and local data acquisition, gateways/datalinks between 

systems and components, operator monitoring and control interfaces, firewalls to external computer 

systems and networks, alarming and archiving functions, and communications between the systems. 

The DCIS is subdivided into the safety-related DCIS (Q-DCIS) and the non-safety-related DCIS 

(N-DCIS). The Q-DCIS uses three diverse platforms: NUMAC (Nuclear Measurement Analysis and 

Control) for the reactor trip and isolation functions (RTIFs), TRICON for SSLC/ESF functions, and 

independent logic controllers for the ATWS/SLC and vacuum breaker (VB) isolation function. The 

N-DCIS includes the diverse protection system (DPS), the nuclear control systems, the plant 
94 

investment protection (PIP) systems, the plant computer and workstations, and the severe accident 

mitigation system (Deluge system). The safety category, the system families, the system architecture, 

and the subsystems in that family are summarized in XTable 6X. 

Table 6. Economic Simplified Boiling Water Reactor hardware/software diversity architecture 

Safety category Safety-related DCIS 

(Q-DCIS) 

Non-safety-related DCIS 

(N-DCIS) 

System families RPS/NMS SSLC/ESF DPS 

Nuclear Control 

Systems, BOP 

DCIS Systems 

Plant computer 

Divisional Triple modular redundant Work-station Architecture 

NUMAC Triconex GE-Mark VIe 

RPS: Reactor Protection System NMS: Neutron Monitoring System 

SSLC: Safety System Logic and Control ESF: Engineered Safety Features 

DCIS: Distributed Control and Information System DPS: Diverse Protection System 

BOP: Balance of Plant 

9.4.1.1 Safety-Related Systems 

Reactor Trip System 

The reactor trip system (RTS) (XFigureX 33) is a four-division, separate- and redundant-protection 

logic-system framework that results in automatic trip and isolation functions. The multidivisional trip 

system includes divisionally separate panels that house the equipment for controlling the various 

safety-related functions and the actuation devices. The RTIF subsystem includes the logics of the RPS 

for reactor scram and the isolation logics for the main steam line isolation valves (MSIVs). The 

neutron monitoring system (NMS) subsystem includes the logics of the SRNM and PRNM functions 

of the NMS. 

One of the major subsystems, or functions, of the RTS is the RPS. The ESBWR RPS is designed to 

provide the capability to automatically or manually initiate a reactor scram while maintaining 

protection against unnecessary scrams resulting from single failures. The RPS logic will not result in 

a reactor trip when one entire division of channel sensors is bypassed and/or when one of the four 

automatic RPS trip logic systems is out-of-service (with any three of the four divisions of 

safety-related power available). This is accomplished through the combination of fail-safe equipment 

design, the redundant sensor channel trip decision logic, and the redundant two-out-of-four trip 

systems output scram logic. 

The RPS is classified as a safety-related system. The RPS electrical equipment is classified as 

Seismic Category I and will be environmentally and seismically qualified. The RPS initiates reactor 

trip signals within individual sensor channels. Reactor scram results if system logic is satisfied. 

Engineered Safety Features Actuation Systems 

The general arrangement of the ESBWR ESF/ECCS also consists of four divisions of redundant 

logic; each division has a main chassis located in the CR area, dedicated Q-DCIS rooms, and remote 

chassis [in the reactor and control buildings (RB and CB)]. All remote chassis connections are 

through redundant fiber as are the connections to the MCR displays and (one way) connections to the 

N-DCIS. All chassis are redundantly powered by both R13 (uninterruptible) and R14 (regulated but 

interruptible) power, and all four divisions can be powered by either diesel generator through the 

isolation load centers. 
95 

Per division, a two-out-of-three (2/3) logic is used to determine whether an ECCS actuation condition 

exists, and then two of four divisions must agree before all four divisions are signaled to operate the 

final actuators. The squib and solenoid actuators are designed such that any one of the four divisions 

(after the 2/3 logic and 2/4 logic) can operate the actuator; however, the actuator cannot be operated 

from a single failure within the division. 

Each of the four independent and separated Q-DCIS channels feeds separate and independent trains 

of SSLC/ESF equipment in the same division. The SSLC/ESF resides in four independent and 

separated instrumentation divisions. The SSLC/ESF integrates the control logic of the safety-related 

systems in each division into firmware or microprocessor-based, software-controlled, processing 

modules located in divisional cabinets in the safety equipment room of the CB. Most SSLC/ESF input 

data are process variables multiplexed via the Q-DCIS in four physically and electrically isolated 

redundant instrumentation divisions. These input data are processed within the remote multiplexing 

unit (RMU) function of the Q-DCIS. The sensor data are then transmitted through the DCIS network 

to the SSLC/ESF digital trip module (DTM) function for setpoint comparison. 

At the division level, the four redundant divisions provide a fault-tolerant architecture that allows 

single division of sensor bypass for online maintenance, testing, and repair, with the intent of not 

losing trip capability. In bypass condition, that is when a division of sensor inputs are bypassed, the 

system automatically defaults to two-out-of-three coincident voting. A trip signal, if necessary, is 

generated from the DTM following setpoint comparison. 

Processed trip signals from its own division and trip signals from the other three divisions are 

transmitted through communication interface and are processed in the voter logic unit (VLU) function 

for two-out-of-four voting. The final trip signal is then transmitted to the RMU function via the 

Q-DCIS network to initiate mechanical actuation devices. There are two independent and redundant 

VLU functional trains (three for the DPV actuation logic) in each division of the SSLC/ESF 

equipment. The vote logic trip signals from each VLU functional train are transmitted to the RMU, 

where a two-out-of-two (or three-out-of-three) confirmation is performed. The redundant trains 

within a division are necessary to prevent single failures within a division from causing a squib 

initiator to fire; as a result, each VLU logic train is required to operate to get an output. Self-tests 

within the SSLC/ESF determine whether any one VLU function has failed, and the failure is alarmed 

in the MCR. To prevent a single I&C failure causing inadvertent actuations, a failed VLU function 

cannot be bypassed for any of the ECCS logic for squib valves initiation. Trip signals are hardwired 

from the RMU to the equipment actuator. 
96 

Figure 33. Reactor protection system functional block (Ref. TD150DT).
97 

9.4.1.2 Non-Safety-Related Systems 

The N-DCIS comprises the non-safety-related portion of the DCIS. The N-DCIS components are 

redundant when they are needed to support power generation and are segmented into systems. 

Segmentation allows, but does not require, the systems to operate independently of each other. The 

N-DCIS uses hardware and software platforms that are diverse from the Q-DCIS. The N-DCIS is a 

network that is dual redundant and at least redundantly powered, so no single failure of an active 

component can affect power generation. The failure is alarmed and can be repaired online. If both 

switches of a segment simultaneously fail, that particular segment is lost. However, the remaining 

segments are unaffected and individual nodes connected to the failed switches may continue to 

function. The remaining switches then automatically reconfigure their uplink ports such that the 

remaining segments automatically find data paths between themselves. 

The individual N-DCIS segments are (1) GEH network, (2) PIP A and B networks, (3) balance of 

plant (BOP) network, and (4) plant computer network. Each network switch can have up to several 

hundred nodes and several uplink ports that are connected to the other switches. All connections to 

the switches are through fiber optic cable network that meets IEEE Std. 383 standard.TPD

151DPT 

9.4.1.3 Communication Systems 

The NUMAC equipment interfaces with both safety-related and non-safety-related equipment. 

For example, NMS and RTIF signals are sent to the safety-related and non-safety-related displays 

providing system operating status as well as trip conditions. It also sends data to the sequence of 

events and transient recording analysis functions. 

Reactor Trip and Isolation Function Communication Interfaces 

A replicated memory network is a shared memory interface that allows each node on the network to 

read and write from the same virtual memory space. A single replicated memory network interface 

module installed in a NUMAC instrument represents a single network node. Data are exchanged 

between the NUMAC microprocessor and the replicated memory network interface module over the 

NUMAC data bus via a dual port RAM interface on the replicated memory network interface module. 

Each replicated memory network interface module is assigned a unique base address such that 

memory read/write operations are restricted to a single network node. A replicated memory network 

comprises multiple network nodes connected via fiber optic cable ring architecture. 

Dual counter-rotating network rings provide a redundant network architecture that is extremely fault 

tolerant. Two network nodes in each instrument, a primary and a secondary, are required to 

implement the dual counter-rotating replicated memory network architecture. Multiple dual 

counter-rotating replicated memory networks are used in the RTIF system to maintain separation 

between safety-related and non-safety-related functions. 

The RTIF safety-related divisional ring network is a dual counter-rotating replicated memory network 

that connects the RMU, DTM, trip logic unit (TLU), and safety-related communication interface 

module (Q-CIM) instruments within a single RTIF division. This network provides the data highway 

for safety-related data to be shared between the RTIF instruments in the division and to make these 

data available to external safety-related systems via the Q-CIM instrument. The Q-CIM is the 

interface between the safety-related divisional ring network and the Q-DCIS network. 

The RTIF non-safety-related divisional ring network is a dual counter-rotating replicated memory 

network that connects the safety-related RMU, DTM, TLU, and Q-CIM instruments to the 

non-safety-related LDU located in the RMU panel in the RB, the non-safety-related LDU located in 
98 

the RTIF panel in the CB, a non-safety-related VDU located in the MCR, and the two RTIF N-CIM 

(non-safety-related CIM) instruments located in a separate nondivisional non-safety-related panel. 

This network provides the data highway for data from the RTIF instruments to be displayed locally 

on the LDU and in the MCR on the VDU and to make these data available to external non-safetyrelated systems via the N-CIM instruments. The N-CIM is the interface between the non-safetyrelated divisional ring network and the N-DCIS network. 

Neutron Monitoring System Communication Interfaces 

A replicated memory network is a shared memory interface that allows each node on the network to 

read and write from the same virtual memory space. A single replicated memory network interface 

module installed in a NUMAC instrument represents a single network node. Data are exchanged 

between the NUMAC microprocessor and the replicated memory network interface module over the 

NUMAC data bus via a dual port RAM interface on the replicated memory network interface module. 

Each replicated memory network interface module is assigned a unique base address such that 

memory read/write operations are restricted to a single network node. A replicated memory network 

comprises multiple network nodes connected via fiber optic cable ring architecture. 

Dual counter-rotating network rings provide a redundant network architecture that is extremely fault 

tolerant. Two network nodes in each instrument, a primary and a secondary, are required to 

implement the dual counter-rotating replicated memory network architecture. Multiple dual 

counter-rotating replicated memory networks are used in the NMS to maintain separation between 

safety-related and non-safety-related functions. 

The NMS safety-related divisional ring network is a dual counter-rotating replicated memory network 

that connects the SRNM RMU, PRNM RMU, DTM, TLU, and Q-CIM instruments within a single 

NMS division. This network provides the data highway for safety-related data to be shared between 

the NMS instruments in the division and to make these data available to external safety-related 

systems via the Q-CIM instrument. The Q-CIM is the interface between the safety-related divisional 

ring network and the Q-DCIS network. 

The NMS non-safety-related divisional ring network is a dual counter-rotating replicated memory 

network that connects the safety-related SRNM RMU, PRNM RMU, DTM, TLU, and Q-CIM 

instruments to the non-safety-related LDU located in the RMU panel in the RB, the non-safety-related 

LDU located in the NMS panel in the CB, a non-safety-related VDU located in the MCR, and to the 

two NMS N-CIM instruments located in a separate nondivisional non-safety-related panel. This 

network provides the data highway for data from the NMS instruments to be displayed locally on an 

LDU and in the MCR on a VDU and to make these data available to external non-safety-related 

systems via the N-CIM instruments. The N-CIM is the interface between the non-safety-related 

divisional ring network and the N-DCIS network. 

Triconex Communication Interfaces 

The communications modules of the Triconex PLC system have three separate communication buses 

which are controlled by three separate communication processors, one connected to each of the three 

main processors. All three bus interfaces merge into a single microprocessor on each communications 

module, so the modules lose their triple redundancy feature at this point. The microprocessor on each 

communications module votes on the messages from the three main processors and transfers only one 

of them to an attached device or external system. If two-way communication is enabled, messages 

received from the attached device are triplicated and transmitted to the three main processors. 
99 

The communication paths to external systems have CRC, handshaking, and other protocol-based 

features, depending on which devices are attached to the communication modules and how the 

communication modules are programmed. These features are supported in both hardware and 

firmware. 

By means of these communications modules, the Triconex PLC system can interface with Modbus 

masters and slaves, other Triconex PLC systems in peer-to-peer networks, external hosts running 

applications over IEEE 802.3 networks, and Honeywell and Foxboro distributed control systems. 

For data sent out to other systems, the main processors broadcast data to the communications modules 

across the communication bus. Data are typically refreshed during every scan and are never more 

than two scan-times old. 

All communication between Q- and N-DCIS is through fiber optics and one way [the only exception 

is Average Power Range Monitor/Low Power Range Monitor (APRM/LPRM) calibration, which can 

only be done by making the affected instrument inoperable]. All communication between divisions 

(to perform 2/4 logic) is also fiber isolated and one way in the sense that no division is dependent on 

any other division for information, timing, data, or the communication itself. 

Almost all communication to/from the field RMUs and almost all communication from the DCIS 

rooms to the CR safety-related and non-safety-related displays are via fiber optics. The few hardwired exceptions are for signals like main turbine trip or reactor SCRAM. These CR considerations 

are important because the communications protocol is such that a melting or otherwise compromised 

fiber will not cause erroneous operation nor affect the continued operation of all automatic safetyrelated or nonsafety systems. This is also supported by the fact that touch screen operation of the 

VDUs deliberately requires several operator actions whose resulting communication is unlikely to be 

replicated by communications loss or damage; similarly the DCIS represents a distributed network 

whose nodal addresses are equally unlikely to be replicated by fiber loss. 

All communication with N-DCIS is one-way (Q-DCIS to N-DCIS) through fiber optics. The loss of 

this communication reportedly will not affect RPS functionality. All communication with other RPS 

divisions is one way, fiber isolated, and does not mix divisional data. 

Mode of Sensor Signal Transmission and Shared Sensor Implementation 

XFigure 34X indicates power and sensor relationships between the various diverse instrumentation and 

control systems. 

Instrumentation and Controls Design Features to Reduce the Probability of Unintended Behaviors 

and/or Latent Faults in the Safety Systems 

Both the RPS and ECCS DCIS systems use different hardware and software than the N-DCIS 

systems, specifically including the DPS, which represents a completely diverse backup design to most 

protection functions in the Q-DCIS. The severe accident deluge system is also diverse from both 

Q-DCIS and N-DCIS. 

The diverse protection system is a triply redundant, non-safety-related, diverse (from RPS/ECCS) 

system that provides an alternate means of initiating reactor trip and actuating selected engineered 

safety-related features and providing plant information to the operator; the relationship is shown in 

XFigure 34X. The DPS receives signals directly from sensors diverse from the safety-related reactor 

protection and ECCS. Specifically the DPS uses hardware, software, and power that are different 

from the safety-related systems. 
100 

Figure 34. Economic Simplified Boiling Water Reactor 

sensors and power diversity (Ref. X150X). 

Using sensors diverse from those used by the RPS, the DPS causes a SCRAM by interrupting the 

current in the 120 VAC return power from the HCU solenoids using the same switches used to 

perform individual control rod SCRAM timing. The 2/3 SCRAM decision of the triply redundant 

processors is sent via three isolated fiber optics to the SCRAM timing panel where they are 2/3 voted 

to open all the solenoid return power switches. The operator will also have the ability to initiate a 

manual DPS SCRAM from either hard switches or the DPS touch screen display. 

The 2/4 sensor logic and 2/3 processing logic is similar to the SCRAM logic, and the operator will 

also have the ability to initiate the above actions from the DPS touch screen display. The ECCS 

subsystems that use four divisional solenoids to initiate flow (SRVs and ICs) will have a fifth 

non-safety-related solenoid to also cause initiation from the DPS (after a 2/3 vote). 

ESF, ECCS, CRHS 

and LD&IS 

(Non-MSIV) LOGIC 

MANUAL INITIATION 

Divisional 

Power

RPS and LD&IS 

(MSIV) LOGIC 

(Includes NMS protective 

functions) 

MANUAL SCRAM 

AND ISOLATION 

(Non-microprocessor) 

RPS 

Sensors 

Divisional 

Power

ATWS/SLC 

(Discrete Programmable 

Logic) 

MANUAL INITIATION 

ATWS/SLC 

Sensors 

Divisional 

Power

ESF 

Sensors 

SAFETY-RELATEDP

*P

Diverse 

Protection 

System

MANUAL INITIATION 

Load Group 

A, B, C Power 

Diverse 

Battery Power 

RPS and LD&IS 

(MSIV) LOGIC 

(Includes NMS protective 

functions) 

BOP Control

Non-safetyrelated 

Sensors

NON-SAFETY-RELATEDP

**P

Load Group 

A, B, C Power 

“A” PLANT 

INVESTMENT 

PROTECTION

“B” PLANT 

INVESTMENT 

PROTECTION

Load Group 

A, B Power 

* For safety-related systems, each box represents a different platform

** For non-safety-related systems, segmented systems are networked but can work independently.

SEVERE ACCIDENT 

DELUGE SYSTEM 

(GDCS Subsystem)

Load Group

A, B, C Power

Diverse 

Battery Power

Permissive

Non-safetyrelated 

Sensors 
101 

9.4.1.4 Human-System Interface Systems 

Information provided in this section is a summary from Reference D152D. 

Safety-Related Human-System Interface 

The operator interfaces with the safety-related systems through a variety of methods. Dedicated 

controls are used for system initiation and logic reset, while system mode changes are made with 

other controls. Safety-related VDUs provide capability for individual safety equipment control, status 

display, and monitoring. The large fixed-position display provides plant overview information. 

The RSS provides a means to safely shut down the plant from outside the MCR. It provides control of 

the plant systems needed to bring the plant to hot shutdown with the subsequent capability to attain 

safe shutdown in the event that the CR becomes uninhabitable. 

Alarm signals provided by the safety system logic and control (SSLC) are directed to the respective 

safety-related alarm processors and provide display information to the divisionally dedicated VDUs. 

The SSLC microprocessors communicate with the respective divisional VDU controllers through the 

Q-DCIS. The divisional VDUs have on-screen control capability and are classified as safety-related 

equipment. These VDUs provide control and display capabilities for individual safety-related 

systems. 

Divisional isolation devices are provided between the safety-related systems and non-safety-related 

communication networks so that failures in the non-safety-related equipment do not affect the ability 

of safety-related systems to perform their design functions. The non-safety-related communication 

network is part of the N-DCIS. Safety-related system process parameters, alarms, and system status 

information from the SSLC are communicated to the N-DCIS through isolation devices for use by 

other equipment connected to the communication network. Spatially and functionally dedicated 

controls, which are safety related, qualified, and divisionally separated, are available in the CR for 

selected operator control functions. These controls communicate with the safety-related system logic 

units. 

Non-Safety-Related Human-System Interface 

Operational control of non-safety-related systems is accomplished through the use of 

non-safety-related on-screen control VDUs. Non-safety-related data are processed through the 

N-DCIS, which provides redundant and distributed instrumentation and control data communications 

networks. Thus, monitoring and control of interfacing plant systems are supported. 

Alarms for entry conditions into the emergency operating procedures are provided by the alarm 

processing units, both safety-related and non-safety-related. Equipment-level alarm information is 

presented by the computer system through the N-DCIS on the MCC VDUs. The fixed position wide 

display panel provides the critical plant operating information such as power, water level, 

temperature, pressure, flow, and status of major equipment. In addition, a mimic display will indicate 

the availability of safety systems. 
102 

9.4.2 Instrumentation and Controls Architecture Platforms 

The I&C architecture is based on (1) the modular digital electronics platform called NUMAC, 

developed by GE and (2) the Tricon PLC from Triconex. 

9.4.2.1 Nuclear Measurement Analysis and Control Platform 

The NUMAC system consists of the main processor, chassis, power supplies, functional modules, and 

software that executes the safety-related logic for the RTS (i.e., RPS, SPTM, SRNM, and PRNM 

functions) and MSIV portions of the LD&IS. The NUMAC platform is a microprocessor-based 

system that executes application programs in firmware that is nonvolatile and not changeable by the 

user during operation. The NUMAC platform provides the digital monitoring and trip functions of the 

RTS described in Section 7.2 of the “ESBWR Design Control Document.”X

150X

 The RTIF and NMS 

systems comprise multiple NUMAC chassis that are housed within the RTIF and NMS panels. The 

term NUMAC may be used to refer to the chassis, modules, and software that comprise the NUMAC 

system. For example, NUMAC software refers to the software that runs on the NUMAC hardware 

platform. 

9.4.2.2 Triconex Platform 

The Tricon PLC system is a fault-tolerant PLC manufactured by Triconex that uses a triple modular 

redundant (TMR) architecture in which three parallel control paths are integrated into a single overall 

system. The system is designed to use two-out-of-three voting with the intent of providing 

uninterrupted process operation with no single point of random hardware failure. A Tricon PLC 

system consists of 1 main chassis and up to 14 expansion chassis. The main chassis contains (1) two 

redundant power supply modules, (2) three main processor modules, 

(3) communications modules, and (4) I/O modules. 

XFigure 35X shows the data flow in the TMR architecture of the Tricon PLC system. When entering the 

input module, the signals from each attached sensor are separated into three isolated paths and sent to 

one of the three main processor modules. The TriBus inter-processor bus performs a two-out-of-three 

vote on data and corrects any discrepancies. This process ensures that each main processor uses the 

same voted data to execute its application program. 

9.5 REGULATORY IMPACT OF FULLY DIGITAL INSTRUMENTATION AND 

CONTROLS ARCHITECTURES IN NUCLEAR POWER PLANTS 

The I&C features for three new reactor designs have been reviewed in this chapter—the U.S. 

Evolutionary Pressurized Reactor (US-EPR) by AREVA NP; the Advanced Pressurized-Water 

Reactor (APWR) by Mitsubishi Heavy Industries; and the Economic Simplified Boiling Water 

Reactor (ESBWR) by GE-Hitachi. The review indicated that these designs use fully digital and 

networked architectures. Some safety-related modules and subsystems in the plants reviewed include 

ASICs, FPGAs, or CPLDs. While the current regulatory process does an excellent job of ensuring 

reliable safety system designs, generic issues whose resolution can enhance the regulatory process for 

digital systems still remain. These include (1) the need for a complete characterization of failure 

modes for digital systems; (2) determining how much V&V should be required for systems that are 

halfway between “simple” (e.g., binary ON, OFF, and/or a small number of combinatorial logic) and 

“complex” (e.g., microprocessor- and/or software-based (i.e., must V&V be required to the same 

level as a computer-based system?)); (3) determining how the surveillance function can be protected 

against a software fault that leads to a common cause failure to detect a failed protection system; and 
103 

Figure 35. Triple modular redundant architecture of the Tricon PLC system. 

(4) determining how much credit should be given to an online diagnostic system, which in itself could 

be more complex than a simple protection system function. 

Other regulatory issues include `the following. 

• The Potential for CCF Due to Identical (Software) Functions in Modules in Redundant Channels 

or Divisions. In addition to the traditional CCF triggering mechanisms (environmental stressors 

and signal transients resulting from a common external source), the sequential transmission of 

corrupted data (e.g., due to a single failure) in software-based systems as a result of some latent 

propagation mechanisms also may result in the failure of multiple trains. 

• Functional and Data Independence between Safety and Nonsafety Systems or Between Safety 

Divisions. The sequential execution of instructions in digital systems, along with response time 

requirements, makes it especially important that a safety system should not depend on data from a 

nonsafety (or another safety) system to perform its safety function. 

• Cyber Security Issues. It becomes crucial that each subsystem (whether safety or nonsafety) be 

critically examined to identify any potential for intrusion from any source, external or internal. It 

is important here to note that the potential for a cyber threat should not only be reviewed from the 

point of view of how an external source can be prevented from gaining access to the system under 

consideration. A subsystem can be a plant vulnerability if it has any flaw that could be exploited 

as part of a cyber attack. The flaw could be a design oversight: malicious online modifications are 

not required if vulnerability already exists. The broader issue, in this case, is whether or not a 

design flaw exists in a subsystem that could be exploited via any communication line connected 

to the subsystem under consideration. 

• Diversity and Defense-in-Depth Issues. For fully digital systems where the backup system is also 

digital, the issue of having adequate defense-in-depth becomes significant. Per Branch Technical 

Position 7-19 (sometimes referred to as BTP 7-19),TPD

153DPT a software CCF is a “beyond design basis” 

event. Thus, adequate coping is judged based on best estimate analysis methods. These include 

nominal initial plant conditions and concurrent failure assumptions. There should be significant 

Auto Spare 

VOTER 

Output 

Leg 

A

Output 

Leg 

B

Output 

Leg 

C

Output 

Termination

Auto Spare 

Input 

Leg 

A 

Input 

Leg 

B 

Input 

Leg 

C 

Input 

Termination 

Main 

Processor

B 

I/O Bus

I/O Bus Main 

Processor

A 

I/O Bus

Main 

Processor

C 

TriBus

TriBus
104 

functional and equipment diversity within the control systems, within the safety systems, and 

between the control and safety systems, and it should be demonstrated that such diversity 

considerably limits the probability for CCFs. Finally, defense-in-depth coping analysis should 

conservatively be based on the assumption that a CCF affects all digital control and protection 

systems in their entirety and that all the control and safety functions controlled by the primary 

safety platform are disabled. 
105 

10. REFERENCES 

T1T. R.T. Wood UetU. UalU., “Emerging Technologies in Instrumentation and Controls,” NUREG/CR6812, Nuclear Regulatory Commission, March 2003. 

T2T. K. Korsah UetU. UalU., “Emerging Technologies in Instrumentation and Controls: An Update,” 

NUREG/CR-6888, Nuclear Regulatory Commission, January 2006. 

T3T. NRC Commission Papers (SECY), “NRC Research Plan for Digital Instrumentation and 

Control”, SECY-01-0155, August 15, 2001.

T4T. Interim Staff Guidance DI&C-ISG-04, “Highly-Integrated Control Rooms—Communications 

Issues (HICRc)”, ML072540138, September 28, 2007.

T5T. M. K. Howlader, K. Korsah, and P. D. Ewing, “Technical Basis for Regulatory Guidance on 

Implementing Wireless Communications in Nuclear Facilities,” ORNL/NRC/LTR-07/09. 

T6T The Tokeneer Project: A hands-on look at an NSA funded, highly secure biometric software 

system, HTUhttp://www.adacore.com/home/gnatpro/tokeneer/UTH, accessed October 2008. 

T7T. J. M. Harper and J. G. Beckerley, Eds., Nuclear Power Reactor Instrumentation Systems 

Handbook, Vol. 1, TIC-25952-P1, U.S. Atomic Energy Commission, 1973. 

T8T. K. O. Hill, Y. Fujii, D. C. Johnson, and B. S. Kawasaki, Photosensitivity in optical fiber 

waveguides: Application to reflection filter fabrication, Applied Physics Letters, Vol. 32, No. 

10, pp. 647–649, May 1978. 

T9T. G. Meltz, W. W. Morey, and W. H. Glenn, Formation of Bragg gratings in optical fibers by a 

transverse holographic method, Optics Letters, Vol. 14, No. 15, pp. 823–825, August 1989. 

T10T. A. D. Kersey and T. A. Berkoff, Fiber-Optic Bragg-Grating Differential-Temperature Sensor,

IEEE Photonics Technology Letters, Vol. 4, No. 10, pp. 1183–1185, October 1992. 

T11T. R. S. Fielder, D. Klemer, and K. L. Stinson-Bagby, High-Temperature Fiber Optic Sensors, an 

Enabling Technology for Nuclear Reactor Applications, Proceedings of ICAPP ‘04, pp. 2295–

305, Pittsburgh, PA, USA, June 13–17, 2004. 

T12T. R. S. Fielder, R. G. Duncan, and M .L. Palmer, Recent Advancements in Harsh Environment 

Fiber Optic Sensors: An Enabling Technology for Space Nuclear Power, Proceedings of the 

Space Nuclear Conference 2005, pp. 476–484, San Diego, California, June 5–9, 2005. 

T13T. A. F. Fernandez, A. I. Gusarov, B. Brichard, S. Bodart, K. Lammens, F. Berghmans, 

M. Decréton, P. Mégret, M. Blondel, and A. Delchambre, Temperature Monitoring Of Nuclear 

Reactor Cores With Multiplexed Fiber Bragg Grating Sensors, Optical Engineering, Vol. 41, 

No. 6, pp. 1246–54, June 2002. 

T14T. A. I. Gusarov, F. Berghmans, O. Deparis, A. F. Fernandez, Y. Defosse, P. Mégret, 

M. Décreton, and M. Blondel, High Total Dose Radiation Effects on Temperature Sensing 

Fiber Bragg Gratings, IEEE Photonics Technology Letters, Vol. 11, No. 9, pp. 1159–61, 

September 1999. 

T15T. L. C. Lynnworth and E. H. Carnevale, Ultrasonic Temperature Measuring Device, NASA CR72339, 1967. 

T16T. G. A. Carlson, W. H. Sullivan, and H. G. Plein, Application of Ultrasonic Thermometry in 

LMFBR Safety Research, 1977 IEEE Ultrasonics Symposium Proceedings, pp. 24–8, Phoenix, 

AZ, October 26–28. 

T17T. L. C. Lynnworth and E. H. Carnevale, Ultrasonic Thermometry Using Pulse Techniques, in 

Temperature: Its Measurement and Control in Science and Industry, Vol. 4, No. 1, pp. 715-32, 

Instrument Society of America, Pittsburgh, PA, 1972,. 

T18T. L. C. Lynnworth, Ultrasonic Measurements for Process Control, AcademicPress, Inc., San 

Diego, CA, 1989. 

T19T. J. B. Garrison and A. W. Lawson, An Absolute Noise Thermometer for High Temperatures and 

High Pressures, Review of Scientific Instruments, Vol. 20, No. 11, pp. 785–94, November 

1949. 
106 

T20T. H. G. Brixy, Temperature Measurement in Nuclear Reactors by Noise Thermometry, Nuclear 

Instruments and Methods, Vol. 97, No. 1, pp. 75–80, November 1971. 

T21T. R. H. Leyse, R. D. Smith, Gamma Thermometer Developments for Light Water Reactors, IEEE 

Transactions on Nuclear Science, Vol.26, No. 1, pp. 934–943, February 1979. 

T22T. ESBWR Design Control Document, Tier 2— Rev. 0— Chapter 7, Instrumentation and Control 

Systems, Appendix A, August 2005. 

T23T. J. Ancsin, Concerning the Stability of Some Base Metal Thermocouples (Chromel, Alumel, 

Nisil, Nicrosil, Ni, versus Pt), Metrologia, Vol. 33, pp. 117–31, 1996. 

T24T. J. Jablin, M. R. Storar, and P. L. Gray, Improved Operating Efficiency Through the Use of 

Stabilized Thermocouples, Journal of Engineering for Gas Turbines and Power, Vol. 122, pp. 

659–6, October 2003. 

T25T. N. A. Burley, Advanced Integrally Sheathed Type N Thermocouple of Ultra-High 

Thermoelectric Stability, Measurement, Vol. 8, No. 1, pp. 36–41, Jan–Mar 1990. 

T26T. A.V. Belevstev, A.V. Karzhavin, and A.A. Ulanowsky, Stability of a Cable Nicrosil-Nisil 

Thermocouple Under Thermal Cycling, in Temperature: Its Measurement and Control in 

Science and IndustryU,U Vol. 7, edited by D. C. Ripple, AIP 2003, pp. 453–7. 

T27T. N. A. Burley, Nicrosil/Nisil Type N Thermocouples, Omega Thermocouple Technical 

Reference, HTUhttp://www.omega.com/temperature/Z/pdf/z041-044.pdfUTH, accessed April 30 2007. 

T28T. ANSI/ISA-67.06.01, “Performance Monitoring for Nuclear Safety-Related Instrument 

Channels in Nuclear Power Plants,” (published 2002). 

T29T. IEC 61784-1, “Digital data communications for measurement and control—Part 1: profile sets 

for continuous and discrete manufacturing relative to fieldbus use in industrial control 

systems,” (published 2001). 

T30T. IEC 61784-3, “Digital data communications for measurement and control—Part 3: Profiles for 

functional safety communications in industrial networks,” (published 2006). 

T31T. FOUNDATION Fieldbus Technical Overview, FD-043 Rev. 3.0, Fieldbus Foundation, 9005 

Mountain Ridge Dr., Bowie Bldg., Suite 190, Austin, TX 78759-5316, USA. 

T32T. IEC 61784-3-1, “Industrial communication networks – Profiles – Part 3-1: Functional safety 

fieldbuses – Additional specifications for CPF 1” (published 2007) 

T33T. IEEE 802.15.1-2005, “Part 15.1: Wireless medium access control (MAC) and physical layer 

(PHY) specifications for wireless personal area networks (WPANs)”, IEEE Computer Society 

(published 2005). 

T34T. IEEE 802.11-2007, “Part 11: Wireless LAN Medium Access Control (MAC) and Physical 

Layer (PHY) Specifications”, IEEE Computer Society (published 2007). 

T35T. IEEE 802.16-2004, “Part 16: Air Interface for Fixed Broadband Wireless Access Systems,” 

IEEE Computer Society (published 2004). 

T36T. IEEE 802.20, “Draft Standard for Local and Metropolotan Area Networks – Standard Air 

Interface for Mobile Broadband Wireless Access Systems Supporting Vehicular Mobility— 

Physical and Media Access Control Layer Specification,” IEEE Computer Society (published 

2008). 

T37T. A. Kadri and J. Jiang, “Potential Applications of Fieldbus and Wireless Technologies in 

Nuclear Power Plants,” NPIC&HMIT 2006, Albuquerque, NM, November 12–16, 2006. 

T38T. C. Carter, “Wireless technogy at TXU power,” EPRI Wireless and RFID Technology workshop 

Workshop, Chcago, IL, August 01, 2006. 

T39T. M. Tariq, “Leveraging existing wirelss investments to support plant reliability improvements at 

Darlington”, EPRI Wireless and RFID Technology workshop Workshop, Chcago, IL, 

August 01, 2006. 

T40T. J. Rosen and B. Nickerson, “EPRI deployment of wireless smart cart concept,” EPRI Wireless 

and RFID Technology workshop Workshop, Chcago, IL, August 01, 2006. 
107 

T41T. Regulatory Guide 1.152, Rev. 2, “Criteria for Use of Computers in Safety Systems of Nuclear 

Power Plants”, U.S. Nuclear Regulatory Commission, January 2006. 

T42T. Regulatory Guide 1.206, “Combined License Applications for Nuclear Power Plants,” U.S. 

Nuclear Regulatory Commission, June 2007. 

T43T. Regulatory Guide 1.209, “Guidelines for Environmental Qualification of Safety-Related 

Computer-Based Instrumentation and Control Systems in Nuclear Power Plants,” U.S. Nuclear 

Regulatory Commission, March 2007. 

T44T. NUREG-0800, Rev. 5, “Standard Review Plan,” U.S. Nuclear Regulatory Commission, March 

2007. 

T45T. Interim Staff Guidance DI&C-ISG-04, “Highly-Integrated Control Rooms—Communications 

Issues (HICRc),” U.S. Nuclear Regulatory Commission, September 2007. 

T46T. R. Kisner et al., “Technical Review Guidance and Acceptance for Digital Communications in 

Highly Integrated Control Rooms,” Draft NUREG/CR, September 2007. 

T47T. M. K. Howlader, K. Korsah, and P. D. Ewing, “Technical Basis for Regulatory Guidance on 

Implementing Wireless Communications in Nuclear Facilities,” ORNL/NRC/LTR-07/09. 

T48T. “Report on Penryn Series Improvements,” Technology @ Intel Magazine, October 2006. 

T49T. B. D. Josephson, “The discovery of tunneling supercurrents,” Reviews of Modern Physics, Vol. 

46, No. 2, pp. 251–255, April 1974. 

T50T. Cooper, L. N., in Lex Prix Nobel en 1972 (Nobel Foundation), p. 64, 1972. 

T51T. D. J. Herrell, “Femtojoule Josephson logic gates,” International Solid State Circuit Conference, 

Philadelphia, 1974. 

T52T. W. Baechtold, TH. Forster, W. Heuberger, and TH. O. Mohr, “Complementary Josephson 

Junction Circuit: A Fast Flip-Flop AND Logic Gate,” IEEE Electronics Letters, Vol. 11, 

No. 10, pp. 203–204, May 1975. 

T53T. Multi-core Processors: Fundamentals, Trends, and Challenges, Embedded Systems 

Conference 2007, ESC351, Imperas, Inc. 

T54T. International Technology Roadmap for Semiconductors, ITRS 2006 Update, 

HTUhttp://www.itrs.net/Links/2006Update/2006UpdateFinal.htmUTH, accessed November 2007. 

T55T. “The High-k Solution,” IEEE Spectrum, HTUhttp://www.spectrum.ieee.org/UTH, accessed October 

2007. 

T56T. R. Jammy and P. Majhi, “CMOS Scaling & Gate Stack Technology Trends,” IEEE 

International Reliability Physics Symposium (IRPS), Reliability Physics Tutorials, Phoenix, 

AZ, April 15–16, 2007. 

T57T. “Transistors Go Vertical,” IEEE Spectrum, HTUhttp://www.spectrum.ieee.org/UTH, accessed November 

2007. 

T58T. R. Kwasnick, “Product Reliability— an Introduction,” IEEE International Reliability Physics 

Symposium (IRPS), Reliability Physics Tutorials, Phoenix, Arizona, April 15-19, 2007. 

T59T. M. White, J. B. Bernstein, “Microelectronics Reliability: Physics-of-Failure Based Modeling 

and Lifetime Evaluation,” JPL Publication 08-5, 2008. 

T60T. HTUhttp://www.micromanipulator.com/applications/index.php?cat=178#UTH, accessed August 2007. 

T61T. H. Okabayashi, “Stress-induced void formation in metallization for integrated circuits,” 

Materials Science and Engineering: R:Reports, Vol. 11, No. 5, pp. 191–241, December 1993. 

T62T. J. F. Ziegler and W. A. Lanlord, “Effect of Cosmic Rays on Computer Memories,” Science, 

Vol. 206, No. 4420, pp. 776–788, November 1979. 

T63T. J. F. Ziegler and H. Puchner, “SER—History Trends and Challenges, A Guide for Designing 

with Memory ICs”, Cypress, 2004. 

T64T. R. Choi and G. Bersuker, “Reliability Implication in CMOS & Gate Stack Scaling,” IEEE 

International Reliability Physics Symposium (IRPS), Reliability Physics Tutorials, Phoenix, 

AZ, April 15–16, 2007. 
108 

T65T. T. Dellin, “Introduction to Integrated Circuit Reliability,” IEEE International Reliability 

Physics Symposium (IRPS), Reliability Physics Tutorials, Phoenix, AZ, April 15–16, 2007. 

T66T. J. Lloyd, “Electromigration... from Black to Blech and Beyond,” IEEE International Reliability 

Physics Symposium (IRPS), Reliability Physics Tutorials, Phoenix, AZ, 

April 15–16, 2007. 

T67T. Personal communication, M. D. Muhlheim, Oak Ridge National Laboratory with H. Puchner, 

Cypress Semiconductor, April 2007. 

T68T. D. K. Schroder, “Negative Bias Temperature Instability (NBTI), Physics, Materials, Process, 

and Circuit Issues”, Arizona State University, Tempe, AZ, August 2005. 

T69T. G. Simon, “Potential Risks of Using New Electronic Component Technologies in I&C Systems 

for Nuclear Power Plants”, presented in IAEA Technical Meeting on “Impact of Modern 

Technology on Instrumentation and Control in Nuclear Power Plants”, Chatou, France, 

September 13-16, 2005. 

T70T. M. Pecht and S. Tiku, “Bogus!,” The IEEE Spectrum Online for Tech Insiders, 

HTUhttp://www.spectrum.ieee.org/may06/3423UTH, accessed June 2007. 

T71T. ARINC Specification 653P1-2, “Avionics Application Software Standard Interface, Part 1 - 

Required Services”, Aeronautical Radio Inc., May 2006. 

T72T. J. Held et al. (editors), “From a Few Cores to Many: A Tera-scale Computing Research 

Overview,” white paper published by Intel Corporation, 2006 

HTUhttp://download.intel.com/research/platform/terascale/terascale_overview_paper.pdfUH , accessed 

July 2007. 

T73T. Intel web page announcement of 80-core CPU research prototype, 

HTUhttp://www.intel.com/research/platform/terascale/teraflops.htmUH, accessed June 2007.T 

74T T. A. Buttari, et al., “SCOP3, A Rough Guide to Scientific Computing On the PlayStation 3,” 

Technical Report UT-CS-07-595, Version 1.0, Innovative Computing Laboratory, University of 

Tennessee Knoxville, May 11, 2007. 

T75T. R. Janardhan and T. Downar, “A Nested FGMRES Method for Parallel Calculation of Nuclear 

Reactor Transients,” Journal of Scientific Computing, Vol. 13, No. 1, pp. 65-93, March, 1998. 

T76T. M. Díaz, et al., “A component-based nuclear power plant simulator kernel,” Concurrency and 

Computation: Practice and Experience, Vol. 19, pp. 593-607, October 2006. 

T77T. Interim Staff Guidance, DI&C-ISG-04, “Highly-Integrated Control Rooms—Communications 

Issues (HICRc),” ML072540138, U.S. NRC, September 28, 2008. 

T78T. L. J. Bond, et al., “On-Line Intelligent Self-Diagnostic Monitoring for Next Generation Nuclear 

Plants”, NERI Project # 99-168, PNNL-14304, Pacific Northwest National Laboratory, 2003. 

T79T. L. J. Bond, et al., “Improved economics of nuclear plant life management,” Second 

International Symposium on Nuclear Power Plant Life Management, October 15-18, 2007, 

Shanghai, China.

T80T. L. J. Bond and S. R. Doctor, “From NDE to Prognostics: A revolution in Asset Management 

for Generation IV Nuclear Power Plants,” Proceedings of SMIRT 19, August 12-17, 2007. 

T81T. G. Wilkowski et al., “Status of Efforts to Evaluate LOCA Frequency Estimates Using 

Combined PRA and PFM Approaches,” 28th MPA Seminar, Materials Testing Institute, 

Universitaet Stuttgart, Germany (2002). 

T82T. J. J. Gertler, Fault Detection and Diagnosis in Engineering Systems, Marcel Dekker, New 

York, 1998. 

T83T. B. R. Upadhyaya, F. Li, N. Samardzija, R. Kephart and L. Coffey, “Development of DataDriven Modeling Methods for Monitoring Coal Pulverizer Units in Power Plants,” Proceedings 

of the 17th Annual ISA POWID/EPRI Controls and Instrumentation Conference and 50th 

Annual ISA POWID Symposium, Pittsburgh, June 2007. 

T84T. K. Zhao, B. R. Upadhyaya and R. T. Wood, “Robust Dynamic Sensor Fault Detection and 
109 

Isolation of Helical Coil Steam Generator Systems Using a Subspace Identification Technique,” 

Nuclear Technology, Vol. 153, pp. 326–340, March 2006. 

T85T. B. Lu and B. R. Upadhyaya, “Monitoring and Fault Diagnosis of the Steam Generator System 

of a Nuclear Power Plant Using Data-Driven Modeling and Residual Space Analysis,” Annals 

of Nuclear Energy, Vol. 32, pp. 897–912, June 2005. 

T86T. B. Lu, B. R. Upadhyaya, and R. B. Perez, “Structural Integrity Monitoring of Steam Generator 

Tubing Using Transient Acoustic Signal Analysis,” IEEE Transactions on Nuclear Science, 

Vol. 52, No. 1, pp. 484–493, February 2005. 

T87T. I. M. Goncalves, D. K. S. Ting, P. B. Ferreira and B. R. Upadhyaya, “Monitoring an 

Experimental Reactor Using the Group Method of Data Handling Approach,” Nuclear 

Technology, Vol. 149, No. 1, pp. 110–121, January 2005. 

T88T. J. W. Hines and E. Davis, “Lessons Learned From the U.S. Nuclear Power Plant On-Line 

Monitoring Programs,” Progress in Nuclear Energy, Vol. 46, No. 3-4, pp. 176–189, 2005. 

T89T. B. R. Upadhyaya and B. Lu, “Data Mining for Monitoring Plant Devices Using GMDH and 

Pattern Classification,” Chapter in Statistical Data Mining and Knowledge Discovery, Edited 

by H. Bozdoğan, pp. 269–279, Chapman & Hall/CRC, Boca Raton, 2004. 

T90T. B. R. Upadhyaya, K. Zhao, and B. Lu, “Fault Monitoring of Nuclear Power Plant Sensors and 

Field Devices,” Progress in Nuclear Energy, Vol. 43, No. 1-4, pp. 337–342, 2003. 

T91T. Proceedings of the 8th Symposium on Nuclear Reactor Surveillance and Diagnostics, Progress 

in Nuclear Energy, Volume 43, No. 1-4, Pergamon Press, 2003. 

T92T. Proceedings of the 8th Symposium on Nuclear Reactor Surveillance and Diagnostics, Progress 

in Nuclear Energy, Volume 43, No. 1-4, Pergamon Press, 2003. 

T93T. N. Kaistha and B.R. Upadhyaya, “Incipient Fault Detection and Isolation of Field Devices in 

Nuclear Power Systems Using Principal Component Analysis,” Nuclear Technology, Vol. 136, 

No. 2, pp. 221–230, November 2001. 

T94T. A.S. Erbay and B. R. Upadhyaya, “A Personal Computer-Based On-Line Signal Validation 

System for Nuclear Power Plants,” Nuclear Technology, Vol. 119, pp. 63–75, July 1997. 

T95T. W. Yan and B. R. Upadhyaya, “An Integrated Signal Processing and Neural Networks System 

for Steam Generator Tubing Diagnostics Using Eddy Current Inspection,” Annals of Nuclear 

Energy, Vol. 23, No. 10, pp. 813–825, 1996. 

T96T. B. R. Upadhyaya, B. Raychaudhuri, J. E. Banks, and M. Naghedolfeizi, “Monitoring and 

Prognosis of Plant Components,” P/PM Technology, Vol. 7, No. 6, pp. 43–49, December 1994. 

T97T. B. R. Upadhyaya, O. Glockler, and J. Eklund, “Multivariate Statistical Signal Processing 

Technique for Fault Detection and Diagnostics,” ISA Transactions, Vol. 29, No. 4, pp. 79-95, 

1990. 

T98T. K. E. Holbert and B. R. Upadhyaya, “An Integrated Signal Validation System for Nuclear 

Power Plants,” Nuclear Technology, Vol. 92, No. 3, pp. 411-427, December 1990. 

T99T. J. Garvey, D. Garvey, R. Seibert, and J.W. Hines, “Validation of On-line Monitoring 

Techniques to Nuclear Plant Data,” Nuclear Engineering and Technology, Vol. 39, No. 2, pp. 

149–158, 2007. 

T100T. P. Howard, “Prognostic Technology—new challenges,” Proceedings of the 59th MFPT, 

Virginia Beach, VA, 2005, pp. 3–8. 

T101T. C. W. Mayo, D. P. Bozarth, G. N. Lagerberg and C. L. Mason, “Loose-parts Monitoring 

System Improvements: Final Report,” EPRI-NP-5743, Electric Power Research Institute 

(EPRI), Palo Alto, CA, March 1988. 

T102T. C. W. Mayo, “Loose Parts Signal Theory,” Progress in Nuclear Energy, Vol. 15, pp. 535–543, 

1985. 
110 

T103T. J.-P. Chiu, S.-S. Shyu and Y.-C. Tzeng, “On-Line Neuro-Expert System for Loose Parts Impact 

Signal Analysis,” presented in Technical Meeting on “Increasing Instrument Calibration 

Interval through On-line Calibration Technologies”, Halden, Norway, September 2004. 

T104T. K. S. Ko and K. I. Han, “Relevance of TSOs in Providing Technical and Scientific Services to 

Operators/Industry,” in Proceedings of an International Conference, “Challenges Faced by 

Technical and Scientific Support Organizations in Enhancing Nuclear Safety,” Aix-enProvence, April 2007. 

T105T. EPRI Report 1006777, “On-line Monitoring Cost-Benefit Guide,” Electric Power Research 

Institute (EPRI), Palo Alto, CA, 2003. 

T106T. “Periodic Testing of Electric Power and Protection Systems,” Regulatory Guide 1.118, 

Rev 3, April 1995 

T107T. IEEE 1023-2004, “IEEE Recommended Practice for the Application of Human Factors 

Engineering to Systems, Equipment and Facilities of Nuclear Power Generating Stations and 

Other Nuclear Facilities,” IEEE Power Engineering Society, New York, NY (published 2004). 

T108T. IEEE 1289-1998, “IEEE Guide for the Application of Human Factors Engineering in the 

Design of Computer-Based Monitoring and Control Displays for Nuclear Power Generating 

Stations,” IEEE Power Engineering Society, New York, NY (published 1998). 

T109T. NUREG-0700, Rev. 2, “Human System Interface Design Review Guidance,” U.S. NRC, 

Washington, DC, 2002. 

T110T. J. Naser, “I&C and Control Room Challenges and Opportunities for Maintaining and 

Modernizing Nuclear Power Plants,” 5th International Topical Meeting on Nuclear Plant 

Instrumentation, Controls, and Human Machine Interface Technology, Albuquerque, NM, 

November 12–16, 2006 

T111T. C.-F. Chung and H.-P. Chou, “Investigation on the Design of Human-System Interface for 

Advanced Nuclear Plant Control Room,” 5th International Topical Meeting on Nuclear Plant 

Instrumentation, Controls, and Human Machine Interface Technology, Albuquerque, NM, 

November 12–16, 2006 

T112T. NUREG-0711, Rev. 2, “Human Factors Engineering Program Review Model,” U.S. NRC, 

Washington, DC, 2004. 

T113T. C. Plot, A. M. Ronan, L. Laux, J. Bzostek, J. Milanski and S. Scheff, “Identification of 

Advanced Human Factors Engineering Analysis, Design and Evaluation Methods,” 5th 

International Topical Meeting on Nuclear Plant Instrumentation, Controls, and Human Machine 

Interface Technology, Albuquerque, NM, November 12–16, 2006 

T114T. J. Reed, “Tailoring Human System Interface Design Guidelines for the AP1000 Nuclear Power 

Plant,” 5th International Topical Meeting on Nuclear Plant Instrumentation, Controls, and 

Human Machine Interface Technology, Albuquerque, NM, November 12–16, 2006 

T115T. P. Bachy-Y-Rita, Y. Danilov, M. Tyler and R. J. Grimm, “Late Human Brain Plasticity: 

Vestibular Substitution with a Tongue BrainPort Human-Machine Interface,” Vol. 4 No. 1-2, 

Enero-Junio, Julio-Diciembre 2005. 

T116T. P. Bachy-Y-Rita and S. W. Kercel, “Sensory Substitution and the Human-Machine Interface,” 

TRENDS in Cognitive Sciences, Vol. 7, No. 12, December 2003. 

T117T. M. N. Louka, M. A. Gustavson and S. T. Edvardsen, “Using Virtual Reality to Support MultiParticipant Human-Centered Design Processes for Control Room Design,” 5th International 

Topical Meeting on Nuclear Plant Instrumentation, Controls, and Human Machine Interface 

Technology, Albuquerque, NM, November 12–16, 2006. 

T118T. C. Cruz-Nera, D. Sandin and T. Defanti, “Virtual Reality: The Design and Implementation of 

the CAVEP

®P

”, Proceedings of the SIGGRAPH 93 Computer Graphics Conference, ACM 

SIGGRAPH, 1993. 
111 

T119T. T. G. Rindahl, M. Neils-r.F. and G. Meyer, “Virtual Reality in Planning and Operations from 

Research Topic to Practical Issue,” 5th International Topical Meeting on Nuclear Plant 

Instrumentation, Controls, and Human Machine Interface Technology, Albuquerque, NM, 

November 12–16, 2006 

T120T. C. F. Chuang and H. P. Chou, “Investigation of Potential Operation Issues of Human-System 

Interface in Lungmen Nuclear Power Project,” IEEE Transactions on Nuclear Science, Vol. 52, 

No. 5, pp. 1004–1008, August 2005. 

T121T. “Human-System Interface Design Review Guidelines,” NUREG-0700, Rev. 2, 

T122T. “Computer-Based Procedure Systems: Technical Basis and Human Factors Review Guidance,” 

NUREG/CR-6634 (BNL-NUREG-52564). 

T123T. IEEE Std. 603-1998, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating 

Stations—Description,” IEEE Power Engineering Society, New York, NY, 1998. 

T124T. ANSI/ANS-4.5-1980, “Criteria for Accident Monitoring Functions in Light-Water-Cooled 

Reactors,” (published 1980). 

T125T. IEEE Std. 497-1981, “IEEE Standard Criteria for Accident Monitoring Instrumentation for 

Nuclear Power Generating Stations,” The Institute of Electrical and Electronics Engineers, Inc., 

New York, NY (published 1981). 

T126T. Regulatory Guide 1.97, Rev. 3, “Instrumentation for Light-Water-Cooled Nuclear Power Plants 

to Assess Plant and Environs Conditions during and following an Accident,” U.S. NRC, 

Washington, DC, 1983. 

T127T. J. Naser, “Minimum Inventory of Human-System Interfaces,” Draft Report, EPRI 1015089, 

Electric Power Research Institute, Palo Alto, CA, December 2007. 

T128T. Interim Staff Guidance DI&C-ISG-05, Highly-Integrated Control Rooms ─ Human Factors 

Issues,” U.S. NRC, Washington, DC, September 2007. 

T129T. R. Torok and J. Naser, “EPRI Training to Support Digital Upgrades in Nuclear Power Plants,” 

NPIC&HMIT 2006, Albuquerque, NM, November 12-16, 2006. 

T130T. “Human Factors Guidance for Control Room and Digital Human-System Interface Design and 

Modification: Guidelines for Planning, Specification, Design, Licensing, Implementation, 

Training, Operation, and Maintenance,” EPRI – 1010042, December 2005. 

T131T. Interim Staff Guidance DI&C-ISG-05, Highly-Integrated Control Rooms ─ Human Factors 

Issues,” U.S. NRC, Washington, DC, September 2007. 

T132T. ISO/IEC 15504-1, “Information technology—Process assessment,” International Organization 

for Standardization/International Electrotechnical Commission, 2004. 

T133T. W. Bogard, “The Bhopal Tragedy”, Westview Press, Boulder Colorado, 1989. 

T134T. Readings of a collection of related references leads the author to state these conclusions, 

namely: D. Whitfield and G. Ord. Some human factors aspects of computer aiding concepts for 

ATCOs. UHuman Factors, 22(5):569–580.U D. E. Embry, Modeling and assisting the operator’s 

diagnostic strategies in accident sequences. In G. Mancini, G. Johnson, et al., editors, UAnalysis, 

Design, and Evaluation of Man—Machine SystemsU, pages 219–224, Pergamon Press, New 

York, 1986. Berndt Brehmer, Development of mental models for decision in technological 

systems. In Jens Rasmussen, et al., editors, UNew Technology and Human Error, Upages 111–120, 

John Wiley & Sons, New York, 1987. C. D. Wickens and C. Kessel, Failure Detection in 

dynamic systems, In Jens Rasmussen, et al., editor, UHuman Detection and Diagnosis of System 

FailuresU, pages 155–170 Plenum Press, New York, 1981. Malcolm J. Brookes, Human factors 

in the design and operation of reactor safety systems, In David Sills, et al., editor, UAccident at 

Three Mile Island: The Human DimensionsU, pages 155–160, Westview Press, Boulder, 

Colorado, 1982. Among others. 

T135T. Adding further references leads to the author’s stated conclusion, see, among others; Brendt 

Bremer, Development of mental models for decision in technological systems. In Jens 
112 

Rasmussen, et al., editors, UNew Technology and Human ErrorU, pages 111–120, John Wiley & 

Sons, New York, 1987. K. D. Duncan, Reflections on fault diagnostic expertise, In Jens 

Rasmussen, et al., editors, UNew Technology and Human Error, Upages 261–269, John Wiley, 

New York, 1987. Donald A. Norman, The ‘problem’ with automation: Inappropriate feedback 

and interaction, not ‘over-automation’, In D. E. Broadbent, et al. editors, UHuman Factors in 

Hazardous SituationsU, pages 137–145, Clarendon Press, Oxford, United Kingdom, 1990. 

T136T. V. A. Carreño, C. A. Muñoz and S. Tahar, Editors, “Theorem Proving in Higher-Order 

Logics,” NASA/CP-2002-211736, August 2002. 

T137T. ISO/IEC 12207:2008, “Systems and software engineering—Software life cycle processes,” 

International Organization for Standardization/International Electrotechnical Commission, 

Geneva, Switzerland (published 2008). 

T138T. The Tokeneer Project: A hands-on look at an NSA funded, highly secure biometric software 

system, HTUhttp://www.adacore.com/home/gnatpro/tokeneer/UTH, accessed October 2008. 

T139T. J. Hyvarinen, OL3 I&C Review Status, ASN/IRSN-NRC-STUK Mtg., March 22, 2007. 

T140T. EPR Design Description, Framatome ANP, Inc., August 2005. 

T141T. Ibid. 

T142T. US-APWR Topical Report, “Safety I&C System Description and Design Process,” MUAP07004-NP R1, Mitsubishi Heavy Industries, July 2007. 

T143T. MELTAC, “Safety System Digital Platform –MELTAC-,” MUAP-07005-NP(R2), Mitsubishi 

Heavy Industries, August 2008. 

T144T. Defense-in-Depth and Diversity, MUAP-07006-NP(R2), Mitsubishi Heavy Industries, June 

2008. 

T145T. Design Control Document for the US-APWR, “Chapter 7, Instrumentation and Controls,” 

MUAP-DC007 Revision 1, Mitsubishi Heavy Industries, August 2008. 

T146T. Licensing Topical Report , “Diversity and Defense-in-Depth Report,” NEDO-33251, GEHitachi Nuclear, August 2007. 

T147T. Licensing Topical Report , “Application of Nuclear Measurement Analysis and Control 

(NUMAC) for the ESBWR Reactor Trip System,” NEDO-33288, GE-Hitachi Nuclear Energy, 

October 2007. 

T148T. Triconex Topical Report, “Nuclear Qualification of Tricon Triple Modular Redundant PLC 

System”, 7286-545-1-A, March 2002. 

T149T. “Planning and Installation Guide for Tricon v9-v10 Systems”, Triconex, February 2006. 

T150T. ESBWR Design Control Document, Tier 2, Chapter 7, “Instrumentation and Control Systems,” 

26A6642AW, Revision 5, GE-Hitachi Nuclear Energy, September 2007. 

T151T. IEEE 383-2003, “IEEE Standard for Qualifying Class 1E Electric Cables and Field Splices for 

Nuclear Power Generating Stations,” Institute of Electrical and Electronics Engineers, New 

York, NY (published 2003). 

T152T. ESBWR Design Control Document, Tier 2, Chapter 18, Revision 5, “Human Factors 

Engineering”, 26A6642BX, GE-Hitachi Nuclear Energy, May 2008. 

T153T. Standard Review Plan, Rev. 5, NUREG 0800, U.S. Nuclear Regulatory Commission, March 

2007.