# Revision 4.3

1/19/10 

# Air Pollution Control Operating Permit

Minor Modification and Preconstruction Approval

Permit Activity Number: BOP090002 Program Interest Number: 41800

Mailing Address Plant Location

MICHAEL TRUBY

GEN MGR EAST REGION

NUSTAR ENERGY CORP LP

PO BOX 149

Paulsboro, NJ 08066 ST LINDEN TERMINAL LLC SHORESIDE

FACILITY

4501 Tremley Point Rd

Linden City

Union County

Initial Operating Permit Approval Date: September 29, 2003

Minor Modification Approval Date: April 13, 2010

Operating Permit Expiration Date: September 28, 2013

This minor modification is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C-9.2).

The equipment at the facility must be operated in accordance with the requirements of this permit.

This approval, in response to your application, merges the provisions of the previously approved operating permit

and the changes from this minor modification into a single comprehensive permit that replaces the one previously

issued. This minor modification includes the requirements for a VOC Control Plan for the float roof tanks pursuant

to N.J.A.C. 7:27-16.2.

Equipment at the facility referenced by this minor modification is not covered by the permit shield, pursuant to the

provisions of N.J.A.C. 7:27-22.17. Pursuant to N.J.A.C. 7:27-22.33(e), this minor modification consists of both a

preconstruction approval and operating permit approval. This operating permit does not include compliance

schedules as part of the approved compliance plan.

The permittee shall submit to the Department and to the EPA on forms provided by the Department, at the addresses

given below, a periodic compliance certification, in accordance with N.J.A.C. 7:27-22.19 and the schedule for

compliance certifications set forth in the compliance plan in this operating permit. The annual compliance

certification reporting period will cover the calendar year ending December 31. The annual compliance

certification is due to the Department and the EPA within 60 days af ter the end of each calendar year during

which this permit was in effect. Forms provided by the Department can be found on the Department's website at:

http://www.nj.gov/dep/enfor cement/compliancecertsair.htm

.

The annual compliance certification report may also be consid ered as your six month deviation report for the period

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section

F, General Provisions and Authorities



# , of this permit, if the annual compliance certification is submitted by January

30.

New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II

Air & Environmental Quality Compliance & Enforcement Air Compliance Branch

401 East State Street, P. O. Box 422 290 Broadway

Trenton, New Jersey 08625-0422 New York, New York 10007-1866 

# CHRIS CHRISTIE 

# D EPARTMENT 

# of E NVIRONMENTAL 

# P ROTECTION 

# BOB MARTIN

Governor Commissioner

Division of Air Quality



# KIM GUADAGNO Bureau of Air Permits



# Lt. Governor 401 E. State Street, 2 nd 

# floor, P.O. Box 27

Trenton, NJ 08625-0027

# Revision 4.3

1/19/10 New Jersey Department of Environmental Protection

Air and Environmental Quality Compliance & Enforcement

Northern Regional Enforcement Office

7 Ridgedale Avenue

Cedar Knolls, New Jersey 07927-4080



# Your facility’s current approved operating permit and any previous versions (e.g. superseded, expired, or

terminated) are now available for download in the PDF format at: http://www.nj.gov/dep/aqpp/. After accessing the

website, click on “Approved Operating Permits” listed under “Reports” and then type in the Program Interested (PI)

Number as instructed on the screen. A RADIUS file fo r your permit, containing Facility Specific Requirements

(Compliance Plan), Inventories, and Compliance Schedules (if needed), can be obtained by contacting your permit

writer. Upon importing this information into your personal computer with RADIUS software, you will have up-todate information in RADIUS format. RADIUS software, instructions, and help are available at the Department's

website at www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00

PM daily, where you may speak to someone about any questions you may have. The Operating Permit Help Line

number is 609-633-8248.

If, in your judgment, the Department is imposing any unreasonable condition of approval in this permit modification

action, you may contest the Department’s decision on the modification and request an adjudicatory hearing pursuant

to N.J.S.A. 52:14b-1 et seq. and N.J.A. C. 7:27-22.32(a). All requests for an adjudicatory hearing must be received

in writing by the Department within 20 calendar days of the date you receive this letter. The request must contain

the information requested in N.J.A.C. 7:27-1.32 and the information on the enclosed Administrative Hearing

Request Checklist and Tracking Form.

The permittee is responsible for submitting a timely and administratively complete operating permit renewal

application. The application is considered timely if it is received at least 12 months before the expiration date of the

operating permit. To be deemed administratively complete, an application for renewal of the operating permit shall

include all of the information required by the application form for the renewal and the information required pursuant

to N.J.A.C. 7:27-22.30(d). However, consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit

the renewal application at least 15 months prior to expiration of the operating permit, so that the Department can

notify the applicant of any deficiencies in the application. This will allow the permittee to correct any deficiencies,

and to better ensure that the application is administratively complete by the renewal deadline. Only applications

which are timely and administratively complete will be eligible for coverage by an application shield. The renewal

application can be found at our website, http://www.state.nj.us/dep/aqpp/downloads/forms/OPRenewal.PDF

.

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html . In addition, CAM Plans must be included as

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification

applications denied, pursuant to N.J.A.C. 7:27-22.3.

If you have any questions regarding this permit approval, please call me at 609-633-3839.

Approved by:

Robert Mann

Bureau of Air Permits

Enclosure

CC: S. Riva, USEPA Region II

# Revision 4.3

1/19/10 

# Administrative Hearing Request **Checklist and Tracking Form**

**I. Document Being Appealed**

**Name of the Facility Program Interest** 

**(PI) Number Permit Activity** 

**Number Issuance** 

**Date**

**ST LINDEN TERMINAL LLC SHORESIDE**

**FACILITY 41800 BOP090002** 

**II. Contact Information**

**Name of Person Requesting Hearing Name of Attorney (if applicable)**

**Address: Address:** 

**Telephone: Telephone:** 

**III. Please include the following information as part of your request:**

A. The date the permittee received the permit decision,

B. One printed and two PDF (or scanned) copies of the document being appealed saved on

two CDs – for submitting to address 1 below;

A PDF (or scanned) copy of all documents being submitted to the Office of Legal Affairs

saved on a CD – for submitting to address 2 below **;** C. The legal and factual questions you are appealing;

D. A statement as to whether or not you raised each legal and factual issues during the

permit application process;

E. Suggested revised or alternative permit conditions;

F. An estimate of the time required for the hearing;

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons;

H. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Departments processing of your hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 E. State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625-0027

Phone: (609) 633-2829

**Signature Date**

# Revision 4.3

1/19/10 

# Administrative Hearing Request **Checklist and Tracking Form**

**IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the**

**permit decision, please include the following information:**

1. The date you or your agent received notice of the permit decision (include a copy of that

permit decision with your hearing request);

2. Evidence that a copy of the request has been delivered to the applicant for the permit

which is the subject of the permit decision;

3. A detailed statement of which findings of fact and/or conclusion of law you are

challenging;

4. A description of your participation in any public hearings held in connection with the

permit application and copies of any written comments you submitted;

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a

right, a reference to the applicable statute or explanation of how your property interests

are affected by the permit decision;

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the

request has been delivered to the clerks of the county and the municipality in which the

project which is the subject of the permit decision is located;

7. Suggested revised or alternative permit conditions;

8. An estimate of the time required for the hearing;

9. A request, if necessary, for a barrier-free hearing location for physically disable persons;

10. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Department’s transmittal of the hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 East State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625

Phone: (609) 633-2829

**Signature Date**

# Revision 4.3

1/19/10 

# Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

TABLE OF CONTENTS

Section A

REASON FOR PERMIT

Section B

DEFINITIONS

Section C

POLLUTANT EMISSIONS SUMMARY

Section D

POLLUTION PREVENTION REPORTING

Section E

GENERAL PROVISIONS AND AUTHORITIES

Section F

STATE-ONLY APPLICABLE REQUIREMENTS

Section G

COMPLIANCE PLAN AND INVENTORIES

# Revision 4.3

1/19/10 

# Section A

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

REASON FOR PERMIT

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which requires the state to issue operating permits to major facilities and minor facilities that are in certain

designated source categories. This is the operating permit for the facility listed on the cover page, which includes a

minor modification for a VOC Control Plan for floating roof storage tanks.

New Jersey has elected to integrate its Title I New Source Review (NSR) preconstruction permits with the new Title

V operating permits instead of issuing separate permits. Consequently, the existing preconstruction permit

provisions that were previously approved for this facility have been consolidated into this permit. This permit may

also include applicable requirements for grandfathered sources.

This permit action consolidates previously approved permit terms and conditions into one single permit for the

facility. The New Jersey Department of Environmental Protection (Department) issues this operating permit

authorizing the facility to operate equipment and air pollution control devices. In the operating permit application,

the facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s

application, the Department has approved this operating permit.

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and

emit up to a level specified for each source operation. The signatories named in the application are responsible for

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules.

# Revision 4.3

1/19/10 

# Section B

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

DEFINITIONS

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying

the permit.

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP).

“The EPA,” or “the Administrator,” means the Administrator of the EPA or his designee.

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons.

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons.

“Grandfathered” means, in reference to equipment or co ntrol apparatus, that construction, reconstruction, or

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976,

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or

control apparatus has occurred since.

“Compliance Plan” means the applicable requirements, mo nitoring requirements, record keeping requirements, and

submittal/action requirements detailed in Section G, Facility Specific Requirements, of the operating permit.

# Revision 4.3

1/19/10 

# Section C

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s Potential to Emit (PTE) emissions summary:

Facility Total Potential to Emit

(tons per year)

Primary Secondary Source Categories

VOC

(total) NO

x 

# CO SO 2 

# TSP

(total) Other

(total) PM 10 

# (total) Pb HAPs

(total)

Emission Unit

Summary 138 23.7 0.104 14.1 1.88 NA 1.88 NA 0.243

Batch Process

Summary NA NA NA NA NA NA NA NA NA

Non-Source Fugitive

Emissions 1 

# NA NA NA NA NA NA NA NA NA

Group

Summary NA NA NA NA NA NA NA NA NA

Total

Emissions 2 

# 138 23.7 0.104 14.1 1.88 NA 1.88 NA 0.243

VOC Volatile Organic Compounds PM 10 

# Particulates under 10 microns

NO

x 

# Nitrogen Oxides Pb Lead

CO Carbon Monoxide HAPs Hazardous Air Pollutants

SO 2 

# Sulfur Dioxide

TSP Total Suspended Particulates

Other Any other air contaminant regulated under the Federal Clean Air Act

1 

# Not applicable to this facility.

2 

# Total emissions from this facility do not include emissions from Insignificant Sources.

# Revision 4.3

1/19/10 

# Section C

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s ha zardous air pollutants (HAP) emissions summary: 3



# HAP TPY

Benzene 0.243

3 

# Do not sum these values for the purpose of establishing a total HAP potential to emit. See previous page for the

allowable total HAP emissions.

# Revision 4.3

1/19/10 

# Section D

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

POLLUTION PREVENTION REPORTING

General Pollution Prevention conditions

The following evaluation requirements are included to track the facility’s progress in several critical areas identified

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with

the air quality standard for the protection of public health . The control of hazardous air pollutants (HAPs) is also a

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels.

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these

air contaminants. Also, as part of significant modification applications, proposed major increases of these air

contaminants requires evaluation of po llution prevention and cross media effects.

The evaluation of these trends requires no increased monito ring. Rather it utilizes existing monitoring data, as

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and

the Department review major source trends periodically, as part of the 5-year renewal review and public comment

process. The Department requests that the facility-wide tr ends be presented on graphs for attachment to the public

information document for the 5-year renewal.

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or

hazardous wastes).

Information to include with the renewal application:

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant

emissions of Volatile Organic Compounds (VOC), Nitr ogen Oxides (NOx), if the facility’s potential to

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or

solid waste) and/or pollution preven tion. Changes should be itemized for each emission unit (or process)

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year

of any HAP. Also, show the net change for the facility.

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a

potential to emit over one ton per year of any HAP. Also, show the net change for the facility.

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject

to reporting under 1 above, on a pound per unit of pr oduct basis, based on annual actual emissions and

annual production over the five year period. Changes should be itemized for each emission unit (or

# Revision 4.3

1/19/10 

# process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton

per year of any HAP. Also, show the net change for the facility.

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP

fugitives, which are subject to reporting under (1) above; explain measures taken to minimize such

fugitives; and provide an explanation for any significant changes.

Information to include with an application for a significant modification to this permit:

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and

HAP air contaminants as part of the significant modifica tion application. If an explanation is provided, the

facility should identify the pollutant and the specific environmental media to which the pollutant is

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to

the air.

# Revision 4.3

1/19/10 

# Section E

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

GENERAL PROVISIONS AND AUTHORITIES

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the

enjoyment of life or property. This shall not include an air contaminant that occurs only in areas over

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations,

including odors, are not considered Federa lly enforceable. [N.J.A.C. 7:27-22.16(g)8]

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be

reported to the Department as follows:

If the air contaminants are released in a quantity or concentration which poses a potential threat to public

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee

shall report the release to the Department:

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the

deviation is identified through source emissions testing, it shall be reported through the source

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall

report the release to the Department as part of th e compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported

through the procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)]

3. The permittee shall comply with all conditions of the operating permit including the approved compliance

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit;

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1]

4. It shall not be a defense for the permittee in an enfo rcement action that it would have been necessary to halt

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit.

[N.J.A.C. 7:27-22.16(g)2]

# Revision 4.3

1/19/10 

# 5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3]

6. The permittee shall furnish to the Department, within a reasonable time, any information that the

Department may request in writing to determine whether cause exists for modifying, revoking and

reissuing, or terminating this operating permit; or to determine compliance with the operating permit.

[N.J.A.C. 7:27-22.16(g)4]

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5]

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C.

7:27-22.16(g)6]

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating

permit to be kept. [N.J.A.C. 7:27-22.16(g)7]

10. The Department and its authorized representatives shall have the right to enter and inspect any facility

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9]

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10]

12. Each permittee shall maintain records of all source em issions testing or monitoring performed at the facility

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained,

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain

all other records required by this operating permit for a period of five years from the date each record is

made. At a minimum, source emission testing or mon itoring records shall contain the information specified

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)]

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department,

on forms provided by the Department, a six month deviation report relating to testing and monitoring

required by the operating permit, not including information for testing and monitoring which have other

reporting schedules specified in the permit. Normally, stack testing reporting is submitted within 45 days

of test completion and continuous monitoring reporting is done quarterly. The six month report must

address other specified monitoring, including, but not limited to, continuous and periodic monitoring data

required by this permit. (See column two and three entitled “Monitoring Requirement” and

“Recordkeeping Requirement,” respectively, in the Facili ty Specific Requirements section of this permit.).

The six month reports for the testing and monitoring performed from January 1 through June 30, shall be

reported by July 30 of the same calendar year; or from July 1 through December 31, shall be reported by

January 30 of the following calendar year. Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports

shall clearly identify all deviations from operating permit requirements, the probable cause of such

deviations, and any corrective actions taken. Any “None” listed in the Submittal/Action Requirement in

the operating permit is not intended to override the six- month deviation report. The report shall be certified

pursuant to N.J.A.C. 7:27-1.39 by a responsible official. Forms provided by the Department can be found

on the Department's website at: http://www.nj.gov/dep/enforcement/compliancecertsair.htm [N.J.A.C.

7:27-22.19(d) 3 and N.J.A.C. 7:27-22.19(e)]

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may

also be considered as your six month deviation report for the period from July 1 through December 31

which is due by January 30 of each year if the annual compliance certification is submitted by January 30.

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but

not limited to NSPS, NESHAP, or MACT.

# Revision 4.3

1/19/10 

# 15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a

provision or condition of the operating permit only if:

i. The violation occurred as a result of an eq uipment malfunction, an equipment start-up or

shutdown, or during the performance of necessary equipment maintenance; and

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)]

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring

protocol during the term of the operating permit. N.J.A.C. 7:27-22.18(j)]

The following paragraphs of this section are included for the permittee's convenience to remind them of their

obligations with certain key applicable requirements. These paragraphs are not enforceable since they paraphrase

areas of the operating permits rule. Also, these paragraphs do not reference all the applicable requirements with

which the permittee must comply.

17. Each owner and each operator of any facility, source operation, or activity to which this permit applies is

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C.

7:27-22.

18. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to

be valid.

19. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate,

calculated as the potential to emit, that exceeds the app licable threshold for reporting emissions set forth in

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating

permit.

20

. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of

this operating permit are met. In the event that there are multiple emission limitations, monitoring,

recordkeeping, and/or reporting requirements for a give n source operation, the facility must comply with all

requirements, including the most stringent.

21. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or

monitoring, to demonstrate compliance with applicable requirements.

22. The permittee shall file a timely and complete application for:

Administrative Amendments;

Seven-Day-Notice changes;

Minor Modifications;

Significant Modifications; and

Renewals.

23. Process monitors must be operated at all times wh en the associated process equipment is operating except

during outage time allowed by Department guidelines/procedures or as outlined in Technical Manual 1005.

The permittee must keep a service log as required.

# Revision 4.3

1/19/10 

# Section F

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

STATE-ONLY APPLI CABLE REQUIREMENTS

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifi cally designate as not being federally enforceable any

permit conditions based only on applicable state requirements. The applicable state requirements to which this

provision applies are listed in the table titled “State-Only Applicable Requirements.”

STATE-ONLY APPLICABLE REQUIREMENTS

The following applicable requirements are not federally enforceable:

SECTION SUBJECT ITEM ITEM # REF. #

E --- 15 ---

G FC --- 3

G FC --- 9

G FC --- 16

# Revision 4.3

1/19/10 

# Section G

Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

COMPLIANCE PLAN AND INVENTORIES

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN)

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION)

• REASON FOR APPLICATION

• NON-SOURCE FUGITIVE EMISSIONS

• INSIGNIFICANT SOURCE EMISSIONS

• EQUIPMENT INVENTORY

• EQUIPMENT DETAILS

• CONTROL DEVICE INVENTORY

• CONTROL DEVICE DETAILS

• EMISSION POINT INVENTORY

• EMISSION UNIT/BATCH PROCESS INVENTORY

• SUBJECT ITEM GROUP INVENTORY

# Revision 4.3

1/19/10 

# Facility Name: ST LINDEN TERMINAL LLC SHORESIDE FACILITY

Program Interest Number: 41800

Permit Activity Number: BOP090002

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

Subject Item and Name Page Number

Facility (FC):

FC ......................................................................................................................... ........................................ 1

Fugitive Emissions (FG):

FG0 – Fugitive Emissions Summary ........................................................................................... ................ 6

Insignificant Sources (IS):

IS1 – No. Fuel Oil Storage Tanks ........................................................................................... ..................... 7

IS2 – Non-Applicable VOC Storage Tanks ....................................................................................... ............ 9

Groups (GR):

GR1 – NESHAP Subpart A and Subpart BBBBBB Requirements for Kb Storage Tanks ......................... 11

GR2 – NESHAP Subpart A and Subpart BBBBBB Requirements for K and Ka Storage Tanks ............. 14

GR3 – Subchapter 16 Requirements for Internal Floating Roof Tanks ........................................................ 17

Emission Units (U):

U12 – Tank 105 – Internal Floating Roof Storage Tank ............................................................................. 38

U15 – Marine Loading......................................................................................................... ......................... 43

U40 – Two Boilers .......................................................................................................... ............................ 51

U100 – Six Internal Floa ting Roof Storage Tanks ............................................................................ .......... 60New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:FCRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1General Provisions: Defines numerous termsused in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]None.None.None.2Control and Prohibition of Open Burning:Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]None.None.Obtain an approved permit: Prior tooccurrence of event (prior to open burning).[N.J.A.C. 7:27- 2]3Prohibition of Air Pollution:Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that resultin air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]None.None.None.4Prevention and Control of Air PollutionControl Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]None.None.Comply with the requirement: Uponoccurrence of event. Upon proclamation bythe Governor of an air pollution alert,warning, or emergency, the permittee shallput the Standby Plan into effect. In addition,the permittee shall ensure that all of theapplicable emission reduction objectives ofN.J.A.C. 7:27-12.4, Table I, II, and III arecomplied with whenever there is an airpollution alert, warning, or emergency.[N.J.A.C. 7:27-12]Page 1 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Emission Offsets Rules. [N.J.A.C. 7:27-18]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Comply with the requirement: Uponoccurrence of event. Submit anadministratively complete application whenapplying for a minor modification pursuantto N.J.A.C. 7:27-22.23 or a significantmodification pursuant to N.J.A.C.7:27-22.24. [N.J.A.C. 7:27-22]6Emissions Statements: Submit an annualemission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreedupon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].Submit an Annual Emission Statement:Annually (if required) electronically by May15 or by any mutually agreed upon date, butnot later than June 15 of each year.[N.J.A.C. 7:27-21]7Compliance Certification: Submit annualcompliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]None.None.Submit an Annual Compliance Certification:Annually to the Department and EPA onforms provided by the Department within 60days after the end of each calendar yearduring which this permit was in effect. Theannual compliance certification reportingperiod will cover the calendar year endingDecember 31. Forms provided by theDepartment can be found on theDepartment's web site at the following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]8Prevention of Air Pollution fromArchitectural Coatings and ConsumerProducts. [N.J.A.C. 7:27-23]None.None.None.9Any operation of equipment which causesoff-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26:2C-19(e)]Other: Observation of plant operations.[N.J.S.A. 26:2C-19(e)].Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A.26:2C-19(e)].Notify by phone: Upon occurrence of event.A person who causes a release of aircontaminants in a quantity or concentrationwhich poses a potential threat to publichealth, welfare or the environment or whichmight reasonably result in citizen complaintsshall immediately notify the Department.Such notification shall be made by callingthe Environmental Action Hotline at (877)927-6337. [N.J.S.A. 26:2C-19(e)]Page 2 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10Prevention of Significant Deterioration(PSD). [40 CFR 52.21]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Comply with the requirement: Uponoccurrence of event. If subject to PSD, thepermittee shall submit an administrativelycomplete application when applying for asignificant modification pursuant toN.J.A.C. 7:27-22.24. [N.J.A.C. 7:27-22]11National Emission Standards for HazardousAir Pollutants (NESHAPS) for Asbestos.[40 CFR 61]Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 61.145 and 61.150when conducting any renovation ordemolition activities at the facility. [40 CFR61]12Protection of Stratospheric Ozone:1) If thepermittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 82 Subparts A, B, E,F, and G. [40 CFR 82]Page 3 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement13Deviation Report: In accordance withN.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department, onforms provided by the Department, acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7.27-22.19(d)3, N.J.A.C.7.27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]None.Other: The permittee shall maintaindeviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].Submit a report: As per the approvedschedule. The six-month reports for otherspecified testing or monitoring required bythe operating permit performed fromJanuary 1 through June 30 shall besubmitted by July 30 of the same calendaryear, and from July 1 through December 31,shall be submitted by January 30 of thefollowing calendar year. The report shall besubmitted to the Regional EnforcementOffice and shall be certified pursuant toN.J.A.C. 7:27-1.39 by the responsibleofficial. Forms provided by the Departmentcan be found on the Department's web site atthe following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]14No person shall combust used oil except asauthorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]None.None.Comply with the requirement: Prior tooccurrence of event (prior to burning usedoil) either register with the Departmentpursuant to N.J.A.C. 7:27-20.3 or obtain apermit issued by the Department pursuantto N.J.A.C. 7:27-8 or 7:27-22, whichever isapplicable. [N.J.A.C. 7:27-20.2(d)]Page 4 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15Prevention of Accidental Releases: Facilitiesproducing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]Other: Comply with 40 CFR 68. [40 CFR68].Other: Comply with 40 CFR 68. [40 CFR68].Other (provide description): Other. Complywith 40 CFR 68 as described in theApplicable Requirement. [40 CFR 68]16For equipment subject to CO2 BudgetTrading Program, comply with N.J.A.C.7:27C. [N.J.A.C. 7:27C]Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Comply with the requirement: Uponoccurrence of event. [N.J.A.C. 7:27C]Page 5 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:FG SummaryRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The owner or operator shall perform amonthly leak inspection of all equipment ingasoline service, as defined in 40 CFR63.11100. For this inspection, detectionmethods incorporating sight, sound, andsmell are acceptable. A logbook shall beused and shall be signed by the owner oroperator at the completion of eachinspection. A section of the log book shallcontain a list, summary description, ordiagram(s) showing the location of allequipment in gasoline service at the facility.Each detection of a liquid or vapor leak shallbe recorded in the log book. When a leak isdetected, an initial attempt at repair shall bemade as soon as practicable, but no laterthan 5 calendar days after the leak isdetected. Repair or replacement of leakingequipment shall be completed within 15calendar days after detection of each leak,except as provided in paragraph (d) of thissection. Delay of repair of leakingequipment will be allowed if the repair isnot feasible within 15 days. The owner oroperator shall provide in the semiannualreport specified in 40 CFR 63.11095(b), thereason(s) why the repair was not feasibleand the date each repair was completed.The owner or operator must comply withthis requirement no later than Jannuary 10,2011. [40 CFR 63.11089(a) through (e)]and. [40 CFR 63.11083(b)]Monitored by visual determination eachmonth during operation. The owner oroperator must comply with this requirementno later than January 10, 2011. [40 CFR63.11089(a)]Other: The owner or operator shall record ina log book foreach leak that is detected thefollowing information:(1) The equipment type and identificationnumber.(2) The nature of the leak (i.e., vapor orliquid) and the method of detection (i.e.,sight, sound, or smell).(3) The date the leak was detected and thedate of each attempt to repair the leak.(4) Repair methods applied ineach attemptto repair the leak.(5) "Repair delayed" and the reason for thedelay if the leak is not repaired within 15calendar days after discovery of the leak.(6) The expected date of successful repair ofthe leak if the leak is not repaired within 15days.(7) The date of successful repair of the leak.[40 CFR 63.11089(g)] and.[40 CFR 63.11094].Submit documentation of compliance: Asper the approved schedule The owner oroperator must submit the following:1. Initial Notification as specified in 40 CFR63.9(b). If your facility is in compliancewith the requirements of this subpart at thetime the Initial Notification is due, theNotification of Compliance Status may besubmitted in lieu of the Initial Notification.The owner or operator must submitadditional notifications specified in 40 CFR63.9, as applicable2. Semiannual compliance report to theAdministrator the number of equipmentleaks not repaired within 15 days afterdetection. For each occurrence of anequipment leak for which no repair attemptwas made within 5 days or for which repairwas not completed within 15 days afterdetection the report shall include:(i) The date on which the leak was detected;(ii) The date of each attempt to repair theleak;(iii) The reasons for the delay of repair; and(iv) The date of successful repair.3. Semiannual excess emissions report,including the information specified inparagraph (2), only for a 6-month periodduring which an excess emission event hasoccurred. If no excess emission events haveoccurred during the previous 6-monthperiod, no report is required.[40 CFR 63.11089(e) and (f)], 40 CFR63.11093(a) and (d)] and. [40 CFR63.11095]Page 6 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:IS1 (4) No. 6 Fuel Oil Storage TanksRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Sulfur Content in Fuel: If the tank containsdistillate fuel for use in Union County NewJersey (Zone 4), the maximum allowablesulfur content is 0.2 percent by weight.If the tank contains No. 4 or heavier gradefuel oil for use in Union County New Jersey(Zone 4), the maximum allowable sulfurcontent is 0.3 percent by weight. [N.J.A.C.7:27- 9.2(a)]Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery, basedon no averaging period. The permittee shallcheck the fuel oil sulfur content on theinvoices/bills of lading. [N.J.A.C.7:27-22.16(o)]None.None.2The operating temperature shall not begreater than 350 degrees F. [N.J.A.C.7:27-22.1]None.None.None.3The vapor pressure of the liquid, excludingthe vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]None.None.None.4The tank shall have no visible emissions,exclusive of water vapor, to the outdooratmosphere. [N.J.A.C. 7:27-22.1]None.None.None.5The tank shall not emit any air contaminantswhich may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]None.None.None.6The tank shall not qualify for anyNESHAPS, MACT, or NSPS air pollutioncontrol standards, excluding the NSPSrequirements to maintain a record of thecontents of the tank, the period of storage ofthese contents, and the maximum true vaporpressure of the liquid stored. [N.J.A.C.7:27-22.1]None.None.None.7The tank's potential to emit each TXS andeach HAP shall not exceed the de minimisreporting thresholds as specified in N.J.A.C.7:27-22, Appendix. [N.J.A.C. 7:27-22.1]None.None.None.8The percentage by weight of all HAPscollectively in the raw material stored in thetank shall be less than 1.0 percent. [N.J.A.C.7:27-22.1]None.None.None.Page 7 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9The owner or operator shall have readilyavailable upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #2 to #8above and (3) attests that the tank is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]None.None.None.Page 8 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:IS2 (4) Non-Applicable VOC Storage TanksRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The operating temperature shall not begreater than 350 degrees F. [N.J.A.C.7:27-22.1]None.None.None.2The vapor pressure of the liquid, excludingthe vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]None.None.None.3The tank shall have no visible emissions,exclusive of water vapor, to the outdooratmosphere. [N.J.A.C. 7:27-22.1]None.None.None.4The tank shall not emit any air contaminantswhich may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]None.None.None.5The tank shall not qualify for anyNESHAPS, MACT, or NSPS air pollutioncontrol standards, excluding the NSPSrequirements to maintain a record of thecontents of the tank, the period of storage ofthese contents, and the maximum true vaporpressure of the liquid stored. [N.J.A.C.7:27-22.1]None.None.None.6The tank's potential to emit each TXS andeach HAP shall not exceed the de minimisreporting thresholds as specified in N.J.A.C.7:27-22, Appendix. [N.J.A.C. 7:27-22.1]None.None.None.7The percentage by weight of all HAPscollectively in the raw material stored in thetank shall be less than 1.0 percent. [N.J.A.C.7:27-22.1]None.None.None.Page 9 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8The owner or operator shall have readilyavailable upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #2 to #8above and (3) attests that the tank is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]None.None.None.Page 10 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:GR1 NESHAP Subpart A and SubpartBBBBBB requirements for Kb storage tanksRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1No owner or operator subject to theprovisions of MACT Subpart A in 40 CFR63 shall build, erect, install, or use anyarticle, machine, equipment, or process toconceal an emission that would otherwiseconstitute noncompliance with a relevantstandard. Such concealment includes, but isnot limited to: (1) The use of diluents toachieve compliance with a relevant standardbased on the concentration of a pollutant inthe effluent discharged to the atmosphere;(2) The use of gaseous diluents to achievecompliance with a relevant standard forvisible emissions. [40 CFR 63.4(b)]None.None.None.2The owner and operator must not usefragmentation or phasing of reconstructionactivities (i.e., intentionally dividingreconstruction into multiple parts forpurposes of avoiding new sourcerequirements) to avoid becoming subject tonew source requirements. [40 CFR 63.4(c)]None.None.None.3The owner or operator must operate andmaintain any affected source at all times,including periods of startup, shutdown, andmalfunction, including associated airpollution control equipment and monitoringequipment in a manner consistent withsafety and good air pollution controlpractices for minimizing emissions.Determination of whether such operationand maintenance procedures are being usedwill be based on information available to theAdministrator which may include, but is notlimited to, monitoring results, review ofoperation and maintenance procedures(including the startup, shutdown, andmalfunction plan required in 40 CFR63.6(e)(3), review of operation andmaintenance records, and inspection of thesource. [40 CFR 63.6(e)(1)(i)]None.None.None.Page 11 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4The owner or operator shall correctmalfunctions as soon as practicable aftertheir occurrence. To the extent that anunexpected event arises during a startup,shutdown, or malfunction, the owner oroperator must comply by minimizingemissions during such a startup, shutdown,and malfunction event consistent with safetyand good air pollution control practices. [40CFR 63.6(e)(1)(ii)]None.None.None.5The owner or operator of an affected sourceshall conduct monitoring as specified in therelevant standard, unless otherwise specifiedby the Administrator. [40 CFR 63.8(b)(1)]None.None.None.6The owner or operator of an affected sourceshall notify the Administrator that the sourcebecomes subject to a relevant standard. Thenotification shall include the information asspecified in 40 CFR 63.9(b)(2). [40 CFR63.9(b)(2)]None.Recordkeeping by other recordkeepingmethod (provide description) uponoccurrence of event. Notification recordsshall be maintained and recorded in a formsuitable and readily available for expeditiousinspection and review for at least 5 yearsfollowing the date of each record. Atminimum, the most two recent years of datashall be retained on site. The remaining 3years of data may be retained off site. Suchfiles may be maintained on microfilm, on acomputer, on a computer floppy disks, onmagnetic tape disks, or on microfiche. [40CFR 63.10(b)(1)]Submit notification: As per the approvedschedule. Within 120 calendar days afterthe source becomes subject to the relevantstandard, if initial startup of the affectedsource is before the effective date of thestandard. [40 CFR 63.9(b)(2)]7The owner or operator of a new orreconstructed major affected source mustprovide a notification of intention toconstruct a new major-emitting affectedsource, or reconstruct a major source thatbecomes a major- emitting affected source,with the application for approval ofconstruction or reconstruction as specifiedin 40 CFR 63.5(d)(1)(i). [40 CFR63.9(b)(4)]None.Recordkeeping by other recordkeepingmethod (provide description) once initially.Notification records shall be maintained andrecorded in a form suitable and readilyavailable for expeditious inspection andreview for at least 5 years following the dateof each record. At minimum, the most tworecent years of data shall be retained on site.The remaining 3 years of data may beretained off site. Such files may bemaintained on microfilm, on a computer, ona computer floppy disks, on magnetic tapedisks, or on microfiche. [40 CFR63.10(b)(1)]Submit notification: As per the approvedschedule. The notification shall besubmitted before start-up but not later than60 days after the effective date of a relevantstandard. [40 CFR 63.5(d)(1)(i)]Page 12 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8The owner or operator of a new orreconstructed affected source must providethe following information to theAdministrator: notification of intention toconstruct a new affected source, reconstructan affected source, or reconstruct a sourcesuch that the source becomes an affectedsource: notification of the actual date ofstartup of the source shall be delivered orpostmarked within 15 calendar days afterthat date. [40 CFR 63.9(b)(5)]None.Recordkeeping by other recordkeepingmethod (provide description) once initially.Notification records shall be maintained andrecorded in a form suitable and readilyavailable for expeditious inspection andreview for at least 5 years following the dateof each record. At minimum, the most tworecent years of data shall be retained on site.The remaining 3 years of data may beretained off site. Such files may bemaintained on microfilm, on a computer, ona computer floppy disks, on magnetic tapedisks, or on microfiche. [40 CFR63.10(b)(1)]Submit notification: Upon occurrence ofevent. [40 CFR 63.9(b)(5)]9The owner or operator shall comply with thecontrol requirements of 40 CFR Part 60,Subpart Kb. [40 CFR 63.11087(f)]Other: The owner or operator shall complywith the control requirements of 40 CFRPart 60, Subpart Kb.[40 CFR 63.11087(f)].Other: The owner or operator shall complywith the control requirements of 40 CFRPart 60, Subpart Kb.[40 CFR 63.11087(f)].Submit notification: Once initially. Theowner or operator must submit aNotification of Compliance Status to theDepartment as specified in 40 CFR 63.9(h).The Notification of Compliance Status mustspecify which of the compliance optionsincluded in Table 1 of 40 CFR 63, SubpartBBBBBB, is used to comply with 40 CFR63, SubpartBBBBBB. [40 CFR63.11087(f)] and. [40 CFR 63.11093(b)]Page 13 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:GR2 NESHAP Subpart A andSubpartBBBBBB requirements for K and Ka storage tanksRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1No owner or operator subject to theprovisions of MACT Subpart A in 40 CFR63 shall build, erect, install, or use anyarticle, machine, equipment, or process toconceal an emission that would otherwiseconstitute noncompliance with a relevantstandard. Such concealment includes, but isnot limited to: (1) The use of diluents toachieve compliance with a relevant standardbased on the concentration of a pollutant inthe effluent discharged to the atmosphere;(2) The use of gaseous diluents to achievecompliance with a relevant standard forvisible emissions. [40 CFR 63.4(b)]None.None.None.2The owner and operator must not usefragmentation or phasing of reconstructionactivities (i.e., intentionally dividingreconstruction into multiple parts forpurposes of avoiding new sourcerequirements) to avoid becoming subject tonew source requirements. [40 CFR 63.4(c)]None.None.None.3The owner or operator must operate andmaintain any affected source at all times,including periods of startup, shutdown, andmalfunction, including associated airpollution control equipment and monitoringequipment in a manner consistent withsafety and good air pollution controlpractices for minimizing emissions.Determination of whether such operationand maintenance procedures are being usedwill be based on information available to theAdministrator which may include, but is notlimited to, monitoring results, review ofoperation and maintenance procedures(including the startup, shutdown, andmalfunction plan required in 40 CFR63.6(e)(3), review of operation andmaintenance records, and inspection of thesource. [40 CFR 63.6(e)(1)(i)]None.None.None.Page 14 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4The owner or operator shall correctmalfunctions as soon as practicable aftertheir occurrence. To the extent that anunexpected event arises during a startup,shutdown, or malfunction, the owner oroperator must comply by minimizingemissions during such a startup, shutdown,and malfunction event consistent with safetyand good air pollution control practices. [40CFR 63.6(e)(1)(ii)]None.None.None.5The owner or operator of an affected sourceshall conduct monitoring as specified in therelevant standard, unless otherwise specifiedby the Administrator. [40 CFR 63.8(b)(1)]None.None.None.6The owner or operator of an affected sourceshall notify the Administrator that the sourcebecomes subject to a relevant standard. Thenotification shall include the information asspecified in 40 CFR 63.9(b)(2). [40 CFR63.9(b)(2)]None.Recordkeeping by other recordkeepingmethod (provide description) uponoccurrence of event. Notification recordsshall be maintained and recorded in a formsuitable and readily available for expeditiousinspection and review for at least 5 yearsfollowing the date of each record. Atminimum, the most two recent years of datashall be retained on site. The remaining 3years of data may be retained off site. Suchfiles may be maintained on microfilm, on acomputer, on a computer floppy disks, onmagnetic tape disks, or on microfiche. [40CFR 63.10(b)(1)]Submit notification: As per the approvedschedule. Within 120 calendar days afterthe source becomes subject to the relevantstandard, if initial startup of the affectedsource is before the effective date of thestandard. [40 CFR 63.9(b)(2)]7The owner or operator of a new orreconstructed major affected source mustprovide a notification of intention toconstruct a new major-emitting affectedsource, or reconstruct a major source thatbecomes a major- emitting affected source,with the application for approval ofconstruction or reconstruction as specifiedin 40 CFR 63.5(d)(1)(i). [40 CFR63.9(b)(4)]None.Recordkeeping by other recordkeepingmethod (provide description) once initially.Notification records shall be maintained andrecorded in a form suitable and readilyavailable for expeditious inspection andreview for at least 5 years following the dateof each record. At minimum, the most tworecent years of data shall be retained on site.The remaining 3 years of data may beretained off site. Such files may bemaintained on microfilm, on a computer, ona computer floppy disks, on magnetic tapedisks, or on microfiche. [40 CFR63.10(b)(1)]Submit notification: As per the approvedschedule. The notification shall besubmitted before start-up but not later than60 days after the effective date of a relevantstandard. [40 CFR 63.5(d)(1)(i)]Page 15 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8The owner or operator of a new orreconstructed affected source must providethe following information to theAdministrator: notification of intention toconstruct a new affected source, reconstructan affected source, or reconstruct a sourcesuch that the source becomes an affectedsource: notification of the actual date ofstartup of the source shall be delivered orpostmarked within 15 calendar days afterthat date. [40 CFR 63.9(b)(5)]None.Recordkeeping by other recordkeepingmethod (provide description) once initially.Notification records shall be maintained andrecorded in a form suitable and readilyavailable for expeditious inspection andreview for at least 5 years following the dateof each record. At minimum, the most tworecent years of data shall be retained on site.The remaining 3 years of data may beretained off site. Such files may bemaintained on microfilm, on a computer, ona computer floppy disks, on magnetic tapedisks, or on microfiche. [40 CFR63.10(b)(1)]Submit notification: Upon occurrence ofevent. [40 CFR 63.9(b)(5)]9The owner or operator must meet one of theemission limit and management practices inTable 1 as specified below at the firstdegassing and cleaning activity after January10, 2011 or by January 10, 2018, whicheveris first.(a) Reduce emissions of total organic HAPor TOC by 95 weight-percent with a closedvent system and control device as specifiedin 40 CFR 60.112b(a)(3); or(b) Equip each internal floating roofgasoline storage tank according to therequirements in 40 CFR 60.112b(a)(1),except for the secondary seal requirementsunder 40 CFR 60.112b(a)(1)(ii)(B) and therequirements in 40 CFR 60.112b(a)(1)(iv)through (ix); or(d) Equip and operate each internal floatingroof gasoline storage tank according to theapplicable requirements in 40 CFR63.1063(a)(1) and (b). [40 CFR63.11087(a)] and. [40 CFR 63.11087(b)]Other: The owner or operator tanks shallperform inspections of the floating roofsystem according to the requirements of 40CFR 60.113b(a) if you are complying withoption 2(b) in Table 1 in 40 CFR 63,SubpartBBBBBB, oraccording to therequirements of 40 CFR 63.1063(c)(1) ifyou are complying with option 2(d) in Table1 in 40 CFR 63,SubpartBBBBBB. [40CFR 63.11087(c)] and.[40 CFR63.11092(e)].Other: The owner shall keep records asspecified in 40 CFR 60.115b if you arecomplying with options 2(a), 2(b), or 2(c) inTable 1 in 40 CFR 63, Subpart BBBBBB,except records shall be kept for at least 5years. If you are complying with therequirements of option 2(d) in Table 1 in 40CFR 63, Subpart BBBBBB,you shall keeprecords as specified in 40 CFR 63.1065 [40CFR 63.11087(e)] and.[40 CFR 63.11094].Submit notification: As per the approvedschedule. The owner or operator submit anInitial Notification as specified in 40 CFR63.9(b). If your facility is in compliancewith the requirements of this subpart at thetime the Initial Notification is due, theNotification of Compliance Status may besubmitted in lieu of the Initial Notification.The owner or operator must submit aNotification of Compliance Status asspecified in 40 CFR 63.9(h). TheNotification of Compliance Status mustspecify which of the compliance optionsincluded in Table 1 of 40 CFR 63, SubpartBBBBBB, is used to comply with thissubpart.The owner or operator must submitadditional notifications specified in 40 CFR63.9, as applicable. [40 CFR 63.11087(d)and (e)], 40 CFR 63.11093(a), (b) and (d)]and. [40 CFR 63.11095(a)(1)]Page 16 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Subject Item:GR3 Subchapter 16 requirements for internal floating roofs.Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The exterior surface of the tank shall bepainted and maintained white. Anyidentification symbols are exempt if thesymbols do not cover more than 20 percentof the external surface of the tank's sides andtop or more than 200 square feet, whicheveris less. [N.J.A.C. 7:27-16.2(b)1]None.None.None.2Applicable VOC storage tanks greater than10,000 gallons, determined to fall underRange III shall be equipped with a floatingroof [N.J.A.C. 7:27-16.2(b)2]None.Other: Maintain on-site, for each tank, for aperiod of at least five years, the records thatspecify each VOC stored and the vaporpressure of each VOC at standardconditions. [N.J.A.C. 7:27-16.2(s)1] &.[N.J.A.C. 7:27-16.22(a)].None.3Storage tanks equipped with gauging and/orsampling systems shall be vapor tight exceptwhen gauging or sampling is taking place.In addition, a floating roof tank, is exemptfrom the vapor-tight condition when thecondition at N.J.A.C. 7:27-16.2(o) is metduring refilling. [N.J.A.C. 7:27-16.2(d)]and. [N.J.A.C. 7:27-16.2(f)9]None.None.None.4Any floating-roof tank shall not be requiredto meet the gap seal requirements atN.J.A.C. 7:27-16.2(l)3i through x while theroof is resting on itslegs during theprocesses of draining, degassing or refillingthe tank. [N.J.A.C. 7:27-16.2(f)5]None.None.None.5Equip each fixed roof support column andwell with a sliding cover that is gasketed orwith flexible fabric sleeves. This conditionapplies before the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)7i]None.None.None.Page 17 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6Equip each ladder well with a gasketedcover. The cover shall be closed at alltimes, with no visible gaps, except when thewell must be opened for access. Thiscondition applies before the tank is refilledafter being degassed for the first time afterMay 19, 2009, but no later than May 1,2020. [N.J.A.C. 7:27-16.2(l)7ii]None.None.None.7Equip each access hatch and gauge floatwell with a cover that is gasketed andbolted. Equip each gauge float well with acover that is either gasketed and weighted orgasketed and bolted. The cover shall beclosed at all times, with no visible gaps,except when the hatch or well must beopened for access. This condition appliesbefore the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1i] &[N.J.A.C. 7:27-16.2(l)7iii]None.None.None.8Equip each gauge hatch/sample well with acover that is gasketed. The cover shall beclosed at all times, with no visible gaps,except when the hatch or well must beopened for access. This condition appliesbefore the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1ii] &[N.J.A.C. 7:27-16.2(l)7iii]None.None.None.9Gasket or cover each adjustable roof legwith a VOC impervious sock at all timeswhen the roof is floating. This conditionapplies before the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1iii] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.Page 18 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10Gasket each rim vent. Rim vents shall beclosed at all times, with no visible gaps,when the roof is floating; and shall be set toopen only when the roof is being floated offthe roof leg supports or when the pressurebeneath the rim seal exceeds themanufacturer's recommended setting. Thiscondition applies before the tank is refilledafter being degassed for the first time afterMay 19, 2009, but no later than May 1,2020.[N.J.A.C. 7:27-16.2(l)1iv] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.11Gasket each vacuum breaker. Vacuumbreakers shall be closed at all times, with novisible gaps, when the roof is floating; andshall be set to open only when the roof isbeing floated off or is being landed on theroof leg supports. This condition appliesbefore the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1v] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.12Equip each open floating roof drain with aslotted membrane fabric cover or otherdevice with an equivalent control efficiencythat covers at least 90 percent of the area ofthe opening. This condition applies beforethe tank is refilled after being degassed forthe first time after May 19, 2009, but nolater than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1vi] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.13Equip each unslotted guidepole well with agasketed sliding cover and a flexible fabricsleeve or wiper. This condition appliesbefore the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1vii] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.Page 19 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement14Equip each unslotted guidepole with agasketed cover at the end of the pole. Thecover shall be closed at all times, with novisible gaps, except when gauging orsampling. This condition applies before thetank is refilled after being degassed for thefirst time after May 19, 2009, but no laterthan May 1, 2020. [N.J.A.C.7:27-16.2(l)1viii] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.15Equip each slotted guidepole with agasketed cover, a pole wiper and a polesleeve. The pole sleeve shall be extendedinto the stored liquid. This conditionapplies before the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1ix] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.16Equip each slotted guidepole having a polefloat with a gasketed cover, a pole wiper,and a pole float wiper. The wiper or seal ofthe pole float shall be at or above the heightof the pole wiper. This condition appliesbefore the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1,2020.[N.J.A.C. 7:27-16.2(l)1x] &[N.J.A.C. 7:27-16.2(l)7iii]None.None.None.17Cover each slotted guidepole opening with agasketed cover at all times, with no visiblegaps, except when the cover must be openedfor access. This condition applies before thetank is refilled after being degassed for thefirst time after May 19, 2009, but no laterthan May 1, 2020. [N.J.A.C.7:27-16.2(l)1xi] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.Page 20 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement18Maintain the pole float in a condition suchthat it floats within the guidepole at all timesexcept when it must be removed forsampling or when the tank is empty. Thiscondition applies before the tank is refilledafter being degassed for the first time afterMay 19, 2009, but no later than May 1,2020.[N.J.A.C. 7:27-16.2(l)1xii] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.19Except for vacuum breakers and rim vents,ensure that each opening in the externalfloating roof shall provide a projectionbelow the liquid surface. This conditionapplies before the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1xiii] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.20Except for vacuum breakers, rim vents, roofdrains, and leg sleeves, equip all otheropenings in the roof with a gasketed coveror seal that is closed at all times, with novisible gaps, except when the cover or sealmust be opened for access. This conditionapplies before the tank is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020.[N.J.A.C. 7:27-16.2(l)1xiv] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.21In lieu of complying with the requirement ofno visible gap at [N.J.A.C. 7:27-16.2 (l)1i,ii, iv, v, viii, xi and xiv], maintain all roofopenings in a leak-free condition at all timesexcept during preventive maintenance,repair, or inspection periods specified at[N.J.A.C. 7:27-16.2 (r)].[N.J.A.C. 7:27-16.2(l)2] & [N.J.A.C.7:27-16.2(l)7iii]None.None.None.Page 21 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement22On or before the date an internal floatingroof tank in Range III is refilled after beingdegassed for the first time after May 19,2009, but no later than May 1, 2020, theowner or operator of the tank shall equip thetank with a rim seal system consisting ofeither:(1)A liquid-mounted primary seal meetingthe requirements for primary seals atN.J.A.C 7:27-16.2(l)3iii, vii and x andhaving no tears or openings; or(2)A primary and a secondary seal meetingthe requirements at N.J.A.C. 7:27-16.2(l)3ithrough x, except that(A)A mechanical shoe primary seal shallhave one end extend a minimum verticaldistance of 15 centimeters (six inches) abovethe stored organic liquid surface and theother end extend into the liquid a minimumof 10 centimeters (four inches) instead ofmeeting the requirement at N.J.A.C.7:27-16.2 (l)3v, and(B)A vapor-mounted wiper primary sealmay be used on a tank with a shell that hasriveted or lap-welded horizontal seamsinstead of the liquid mounted or mechanicalshoe primary seal required at N.J.A.C.7:27-16.2 (l)3i. [N.J.A.C. 7:27-16.2(l)7iv]None.None.None.Page 22 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement23The owner or operator shall equip the tankwith a rim seal system meeting the followingrequirements prior to the date the tank isrefilled after being degassed for the firsttime after May 19, 2009, but no later thanMay 1, 2020 (see N.J.A.C. 7:27-16.2(l)7ivfor clarification):i.The primary seal shall be a mechanicalshoe or liquid mounted;ii.The secondary seal shall be rim mountedand shall not be attached to the primary seal;iii.Gaps between the tank shell and theprimary seal shall not exceed 1.3 centimeters(1/2 inch) for a cumulative length of 30percent of the circumference of the tank, and0.32 centimeters (1/8 inch) for 60 percent ofthe circumference of the tank. No gapbetween the tank shell and the primary sealshall exceed 3.8 centimeters (1-1/2 inches).No continuous gap between the tank shelland the primary seal greater than 0.32centimeters (1/8 inch) shall exceed 10percent of the circumference of the tank;iv.Gaps between the tank shell and thesecondary seal shall not exceed 0.32centimeters (1/8 inch) for a cumulativelength of 95 percent of the circumference ofthe tank. No gap between the tank shell andthe secondary seal shall exceed 1.3centimeters (1/2 inch);v.Mechanical shoe primary seals shall beinstalled so that one end of the shoe extendsinto the stored organic liquid and the otherend extends a minimum vertical distance of61 centimeters (24 inches) above the storedorganic liquid surface;Continued below: [N.J.A.C. 7:27-16.2(l)3]None.None.None.Page 23 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement24Continued from above:The owner or operator shall equip the tankwith a rim seal system meeting the followingrequirements prior to the date the tank isrefilled after being degassed for the firsttime after May 19, 2009, but no later thanMay 1, 2020 (see N.J.A.C. 7:27-16.2(l)7ivfor clarification):vi.The geometry of the shoe shall be suchthat the maximum gap between the shoe andthe tank shell is no greater than doubled thegap allowed by the seal gap criteria specifiedin N.J.A.C. 7:27-16.2 (l)3iii for a length ofat least 46 centimeters (18 inches) in thevertical plane above the liquid surface;vii.The primary seal envelope shall bemade available for unobstructed inspectionby the Department, upon request, along itscircumference. In the case of riveted tankswith resilient filled primary seals, at leasteight such locations shall be made available;for all other types of seals, at least four suchlocations shall be made available. If theDepartment deems it necessary, furtherunobstructed inspection of the primary sealmay be required to determine the seal'scondition along its entire circumference;viii.The secondary seal shall be installedin a way that permits probes up to 3.8centimeters (1-1/2 inches) in width to beinserted to measure gaps in the primary seal;Conitnued below: [N.J.A.C. 7:27-16.2(l)3]None.None.None.Page 24 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement25Continued from above:The owner or operator shall equip the tankwith a rim seal system meeting the followingrequirements prior to the date the tank isrefilled after being degassed for the firsttime after May 19, 2009, but no later thanMay 1, 2020 (see N.J.A.C. 7:27-16.2(l)7ivfor clarification):ix.There shall be no holes, tears oropenings in the secondary seal or in theprimary seal envelope surrounding theannular vapor space enclosed by the roofedge, seal fabric, and secondary seal; andx.Except during preventive maintenance,repair, or inspection periods specified at (r)below that do not exceed 72hours, both theprimary seal and the secondary seal shallcover the annular space between the floatingroof and the wall of the storage tank in acontinuous fashion, as required at N.J.A.C.7:27-16.2 (l)3iii and iv. [N.J.A.C.7:27-16.2(l)3]None.None.None.26For an internal floating roof installed priorto July 23, 1984, ensure that theconcentration of organic vapor in the vaporspace above the internal floating roof shallnot exceed 50 percent of its lower explosivelimit. This condition applies before the tankis refilled after being degassed for the firsttime after May 19, 2009, but no later thanMay 1, 2020.[N.J.A.C. 7:27-16.2(l)7v]None.None.None.27For an internal floating roof installed afterJuly 23, 1984, ensure that the concentrationof organic vapor in the vapor space abovethe internal floating roof shall not exceed 30percent of its lower explosive limit. Thiscondition applies before the tank is refilledafter being degassed for the first time afterMay 19, 2009, but no later than May 1,2020. [N.J.A.C. 7:27-16.2(l)7vi]None.None.None.Page 25 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement28If the tank was constructed or installed on orafter December 17,1979, the tank shall beprovided with a double seal floating roof orother control apparatus approved by theDepartment as being equally or moreeffective in preventing the emission of anyVOC into the outdoor atmosphere. Thisrequirement shall remain in effect for anysuch tank until N.J.A.C. 7:7-16.2(l)3, 5, 6 or7 becomes applicable for that tank. Thiscondition applies before the tank is refilledafter being degassed for the first time afterMay 19, 2009, but no later than May 1,2020. [N.J.A.C. 7:27-16.2(l)8i]None.None.None.29If the tank was constructed or installed priorto December 17,1979, the requirements ofN.J.A.C. 7:27-16.2(l)3, 5, 6 or 7 shall applyas applicable. This condition applies beforethe tank is refilled after being degassed forthe first time after May 19, 2009, but nolater than May 1, 2020.[N.J.A.C. 7:27-16.2(l)8ii]None.None.None.30The roof shall float on the liquid surface atall times, except during initial fill and duringthose intervals when the storage vessel iscompletely emptied or subsequently emptiedand refilled. [N.J.A.C. 7:27-16.2(m)]None.None.None.31When performing a roof landing of aninternal floating roof tank:1. When the roof is resting on its legsupports or suspended by cables or hangers,the process of filling, emptying, or refillingshall be continuous and shall beaccomplished as rapidly as possible; and2. After the tank is refilled after beingdegassed for the first time after May 19,2009, any in-service roof landing shall bewith the landed height of the floating roof atits minimum setting.[N.J.A.C. 7:27-16.2(o)]None.Other: Maintain on-site for each tank, forfive years, the records of the roof landingemission information required at N.J.A.C.7:27-21.5(j)1, the records of each floatingroof landing event including, but not limitedto, tank contents before landing and afterrefilling; landed height of the floating roof;height of any liquid remaining in the bottomof the tank after landing; duration oflanding; landing emissions calculated usingAP-42, Chapter 7 methodology, and anyother records needed to create the "FloatingRoof Landing Emission Summary Report"required at N.J.A.C. 7:27-21.5(j)2.[N.J.A.C. 7:27-16.2(s)2 &3] and.[N.J.A.C.7:27-16.22(a)].None.Page 26 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement32The owner or operator of any floating rooftank used to store a VOC shall:Submit a complete facility-wide tank VOCcontrol plan to the Department for approvalat the address listed at N.J.A.C. 7:27-16.2(v)for any floating roof tank existing as of May19, 2009 and an emissions averaging plan tooperate all Range III floating roof tanks thatstore gasoline such that their average annualin-service roof landing VOC emissions, ascalculated in accordance with Chapter7.1.3.2.2 "Roof Landings" of AP-42, assupplemented or amended and, or ascalculated using another method approvedby the Department in accordance withN.J.A.C. 7:27-16.2(v) and after applyingany applicable control efficiencies, is lessthan:(1) Five tons per tank per calendar yearfrom 2011 through 2013;(2) Four tons per tank per calendar yearfrom 2014 through 2016;(3) Three tons per tank per calendar yearfrom 2017 through 2019; and(4) Two tons per tank per calendar year in2020 and subsequent years.[N.J.A.C. 7:27-16.2(p)1] and. [N.J.A.C.7:27-16.2(p)2iii]None.None.Submit documentation of compliance: Asper the approved schedule. Facility-widetank VOC control plan was submittted withoperating permit modification BOP090002prior to December 1,2009. [N.J.A.C.7:27-16.2(p)]Page 27 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement33On and after May 1, 2010, any part of adegassing and cleaning operation of astationary storage tank performed during theperiod May 1 through September 30 shall beperformed only as follows: The owner oroperator shall degas a tank storing a VOCwith a vapor pressure equal to or greaterthan 0.5 psia at standard conditions asfollows:i. Empty the tank of the VOC liquid;ii. Minimize VOC vapors in the tank vaporspace by one of the following methods:(1)Exhaust VOCs contained in the tankvapor space to a vapor control system ratedat a minimum 95 percent efficiency until theorganic vapor concentration is 5,000 partsper million by volume (ppmv) or less asmethane, or is 10 percent or less of thelower explosive limit, whichever is less;(2)Displace VOCs contained in the tankvapor space to a vapor control system ratedat a minimum 95 percent efficiency byfilling the tank with a suitable liquid until 90percent or more of the maximum operatinglevel of the tank is filled. Suitable liquidsare organic liquids having a TVP of lessthan 0.5 psia, water, clean produced water,or produced water derived from crude oilhaving a TVP less than 0.5 psia; or(3)If the tank is a free-water knockout tank,a person may degas the tank vapor space byrestricting the outflow of water and floatingoff the oilpad, such that at least 90 percentof the tank volume is displaced.[N.J.A.C. 7:27-16.2(q)1i] and. [N.J.A.C.7:27-16.2(q)1ii]Other: Monitored by work practicesused.[N.J.A.C. 7:27-22.16(o)].Other: Maintain on-site readily availablerecords of all tank degassing activities foreach tank.[N.J.A.C. 7:27-22.16(o)].None.Page 28 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement34On and after May 1, 2010, any part of adegassing and cleaning operation of astationary storage tank performed during theperiod May 1 through September 30 shall beperformed only as follows: The owner oroperator shall degas a tank storing a VOCwith a vapor pressure equal to or greaterthan 0.5 psia at standard conditions asfollows:iii. Discharge or displace the VOC vaporscontained in the tank vapor space to a vaporcontrol system that is vapor-tight and freeof liquid leaks; andiv. As appropriate, temporarily remove forno longer than one hour, a suitable tankfitting, such as a manway, to facilitateconnection to an external vapor controlsystem.[N.J.A.C. 7:27-16.2(q)1iii] and. [N.J.A.C.7:27-16.2(q)1iv]Other: Monitored by work practicesused.[N.J.A.C. 7:27-22.16(o)].Other: Maintain on-site readily availablerecords of all tank degassing activities foreach tank.[N.J.A.C. 7:27-22.16(o)].None.35On and after May 1, 2010, any part of adegassing and cleaning operation of astationary storage tank performed during theperiod May 1 through September 30 shall beperformed only as follows: The owner oroperator shall clean a tank storing a VOCwith vapor pressure equal to or greater than0.5 psia at standard conditions only if:i.At least one of the following cleaningagents is used:(1)Diesel fuel;(2)A solvent with an initial boiling pointof greater than 302 degrees Fahrenheit;(3)A solvent with a vapor pressure lessthan 0.5 psia;(4)A solvent with 50 grams per liter VOCcontent or less; or(5)Some other Department-approvedcleaning agent; orii.Steam cleaning is performed. [N.J.A.C.7:27-16.2(q)2]Other: Cleaning agentcharacteristics[N.J.A.C. 7:27-22.16(o)].Other: Maintain on-site readily availablerecords of all tank degassing activities foreach tank.[N.J.A.C. 7:27-22.16(o)].None.Page 29 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement36On and after May 1, 2010, any part of adegassing and cleaning operation of astationary storage tank performed during theperiod May 1 through September 30 shall beperformed only as follows: The owner oroperator shall control emissions from thesludge removed from a tank that stores aVOC with a vapor pressure equal to orgreater than 1.5 psia at standard conditionsby:i. During sludge removal, controllingemissions from the receiving vessel byoperating a vapor control system thatreduces VOC emissions by at least 95percent;ii. Transporting removed sludge incontainers that are vapor-tight and free ofliquid leaks; andiii. Storing removed sludge, until finaldisposal, in containers that are vapor-tightand free of liquid leaks, or in tanks thatcomply with N.J.A.C. 7:27-16.2(b).[N.J.A.C. 7:27-16.2(q)3]Other: Monitored by work practicesused.[N.J.A.C. 7:27-22.16(o)].Other: Maintain on-site readily availablerecords of all tank sludge removal activitiesfor each tank.[N.J.A.C. 7:27-22.16(o)].None.Page 30 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement37The owner or operator of a VOC stationarystorage tank in Range III shall have aninspection performed by an authorizedinspector and maintain the tank as follows:1. The findings of any tank inspection,whether completed or not, shall be recordedon the Inspection Form at N.J.A.C. 7:27-16Appendix II, incorporated herein byreference, in accordance with the rule'srequirements. If an inspection is stoppedbefore completion, indicate the reason forthis action in section J "Comments" of theInspection Form;2. During the inspection, the authorizedinspector performing the inspection musthave a copy of the relevant portions of thePreconstruction Permit or the OperatingPermit pertinent to the tank being inspected.The authorized inspector shall compare thepermit to the existing tank and actualoperating conditions of the tank. Theauthorized inspector shall record anydiscrepancies between the permit equipmentdescription and the existing tank, or thepermit conditions and the actual operatingconditions of the tank, as verified during aninspection, in section J "Comments" of theInspection Form;3. Annually inspect the ground levelperiphery of each tank for possible leaks inthe tank shell. Complete section D "GroundLevel Inspection" of the Inspection Form;4. Annually complete all necessarycalculations and record all required dataaccordingly in the Inspection Form andFugitive Emissions Form at N.J.A.C.7:27-16 Appendix II.[N.J.A.C. 7:27-16.2(r)1-3] and. [N.J.A.C.7:27-16.2(r)4]Other: Perform inspection by an authorizedinspector and maintain the tank. During theinspection, the authorized inspectorperforming the inspection must have a copyof the relevant portions of the OperatingPermit pertinent to the tank being inspected.The authorized inspector shall compare thepermit to the existing tank and actualoperating conditions of the tank. Annuallyinspect the ground level periphery ofeachtank for possible leaks in the tank shell.[N.J.A.C. 7-16.2(r)1-3] and.[N.J.A.C.7:27-16.2(r)4].Other: The owner or operator shall annuallycomplete all necessary calculations andrecord all required data accordingly in theInspection Form and Fugitive EmissionsForm at N.J.A.C. 7:27-16 Appendix II. Theauthorized inspector shall record anydiscrepancies between the permit equipmentdescription and the existing tank, or thepermit conditions and the actual operatingconditions of the tank, as verified during aninspection, in section J "Comments" of theInspection Form.The findings of any tank inspection, whethercompleted or not, shall be recorded on theInspection Form at N.J.A.C. 7:27-16,Appendix II. If an inspection is stoppedbefore completion, indicate the reason forthis action in section J "Comments" of theInspection Form.Maintain all inspection reports for thelifetime of each tank.[N.J.A.C. 7:27-16.2(r)1, 2 & 4]and.[N.J.A.C. 7:27-16.2(s)5].None.Page 31 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement38For an internal floating roof tank in RangeIII, the owner or operator shall demonstratecompliance with N.J.A.C. 7:27-16.2(l) byperforming the requirements at N.J.A.C.7:2716.2(r)6 as follows;i. Annually, using an explosimeter,measuring the organic vapor concentrationin the vapor space above the floating roof interms of the lower explosive limit (LEL),and recording the reading in section E of theInspection Form;ii. Annually, from an opening in the domedor fixed roof, visually inspecting the roof tocheck for permit and rule violations, andvisually checking the roof for unsealed rooflegs, open hatches, open emergency roofdrains, or open vacuum breakers. Indicatepresence of any tears in the fabric of thevisible seal. Record the findings undersection F of the Inspection Form; andiii. Each time the tank is degassed, but noless than once every 10 years, performingthe requirements at N.J.A.C. 7:27-16.2(r)5ii(excluding EPA Method 21), iii and iv.[N.J.A.C. 7:27-16.2(r)8]Other: Perform inspections pursuant toN.J.A.C. 7:27-16.2(r)6. [N.J.A.C.7:27-16.2(r)8] and.[N.J.A.C. 7:27-16.22(a)].Other: The owner or operator shall maintainon-site, for each tank for the lifetime of thetank, all inspection reports required pursuantto N.J.A.C. 7:27-16.2(r)6.[N.J.A.C.7:27-16.2(s)5].None.Page 32 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement39Any VOC stationary storage tank in RangeIII shall repair or replace any piping, valve,vent, seal, gasket, or cover of a roof openingthat:i. Is defective;ii. Has a visible gap or is not leak-free; oriii. Does not meet any applicablerequirement of this section [N.J.A.C.7:27-16.16(r)10]None.Other: Maintain on-site, for each tank, for atleast 5 years, the repair and replacementdocumentation. [N.J.A.C 7:27-16.2(s)8]and.[N.J.A.C. 7:27-22.16(a)].Repair equipment: As per the approvedschedule Perform the repair or replacement:i. If the tank is already degassed, prior tofilling; orii. If the tank is not degassed, within 45 daysafter discovery of the needed repair orreplacement. If a repair cannot becompleted and the vessel cannot be emptiedwithin 45 days, the owner or operator mayuse up to two extensions of up to 30additional days each. Documentation of theowner or operators decision to use anextension shall include a description of thefailure, shall document that alternativestorage capacity is unavailable, and shallspecify a schedule of actions that will ensurethat the control equipment will be repairedor the vessel will be completely emptied assoon as practicable. [N.J.A.C.7:27-16.2(r)11]40The owner or operator shall maintainon-site, for each tank, for the time periodspecified at N.J.A.C. 7:27-16.22(a), therecords of all tank integrity testing schedulesfor Range III tanks that N.J.A.C.7:1E-4.2(c)1v requires to be included in the"Discharge, Prevention, Containment andCountermeasure Plan". [N.J.A.C.7:27-16.2(s)7]None.Other: Maintain readily accessible recordspursuant to N.J.A.C.7:27-16.2(s)7.[N.J.A.C. 7:27-16.22(a)].None.41If, during an inspection required at N.J.A.C.7:27-16.2(r), or at any other time, the owneror operator determines that a tank does notcomply with N.J.A.C. 7:27-16.2(l), theowner or operator shall submit a writtenreport to the Department including the causeof the non-compliance, corrective actions toachieve compliance and measures taken toprevent a re-occurrence of thenon-compliance. If the facility has anoperating permit, in accordance withN.J.A.C. 7:27-22, the owner or operatorshall include this report as part of theperiodic compliance reports required atN.J.A.C. 7:27-22.19(d) and (f). [N.J.A.C.7:27-16.2(u)]None.None.Submit a report: As per the approvedschedule , pursuant to N.J.A.C.7:27-16.2(u). [N.J.A.C. 7:27-16.2(u)]Page 33 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement42VOC (Total) < 5 tons/yr average fromin-service roof landings (as defined atN.J.A.C. 7:27-16.1) for all tanks storinggasoline in GR3 during the calendar years2011, 2012, and 2013. Applies to tanks E1,E2, E5, E6, E7, E8 and E12. [N.J.A.C.7:27-16.2(p)2iii]VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year. For all Range III tanks inGR3 that are actually used to store gasolineat some point during the calendar year, theowner or operator shall calculate theemissions resulting from in-service rooflandings (as defined at N.J.A.C. 7:27-16.1)each month during operation, using themethodology described in Chapter 7.1.3.2.2of AP-42 (November 2006 or later version)and applying any applicable controlefficiencies. The total sum-to-date shall becalculated by adding the total in-service rooflanding emissions for all tanks in the GR3that are actually used to store gasoline atsome point during the calendar year for themonth to the total in-service roof landingemissions for the previous months duringthe calendar year. The average-to-date shallbe calculated by dividing the totalsum-to-date emissions by the number oftanks in the GR3 that are actually used tostore gasoline at some point during thecalendar year. Any tank in the GR3 thatdoes not store gasoline at some point duringa particular calendar year shall not beincluded when calculating the sums-to-dateor averages-to-date for that year. Thisprocedure will begin in January 2011.[N.J.A.C. 7:27-16.16(p)2iii] and. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. For the Range III tanks in GR3that are actually used to store gasoline atsome point during the calendar year, theowner or operator shall record the rooflanding emissions for each tank for themonth, the total roof landing emissions forthe month, the sum-to-date of the totalin-service roof landing emissions for themonth and the average-to-date of thein-service roof landing emissions for themonth. [N.J.A.C. 7:27-22.16(o)]None.Page 34 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement43VOC (Total) < 4 tons average fromin-service roof landings (as defined atN.J.A.C. 7:27-16.1) for all tanks storinggasoline in GR3 during the calendar years2014, 2015, and 2016. Applies to tanks E1,E2, E5, E6, E7, E8 and E12. [N.J.A.C.7:27-16.2(p)2iii]VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year. For all Range III tanks inGR3 that are actually used to store gasolineat some point during the calendar year, theowner or operator shall calculate theemissions resulting from in-service rooflandings (as defined at N.J.A.C. 7:27-16.1)each month during operation, using themethodology described in Chapter 7.1.3.2.2of AP-42 (November 2006 or later version)and applying any applicable controlefficiencies. The total sum-to-date shall becalculated by adding the total in-service rooflanding emissions for all tanks in the GR3that are actually used to store gasoline atsome point during the calendar year for themonth to the total in-service roof landingemissions for the previous months duringthe calendar year. The average-to-date shallbe calculated by dividing the totalsum-to-date emissions by the number oftanks in the GR3 that are actually used tostore gasoline at some point during thecalendar year. Any tank in the GR3 thatdoes not store gasoline at some point duringa particular calendar year shall not beincluded when calculating the sums-to-dateor averages-to-date for that year. Thisprocedure will begin in January 2011.[N.J.A.C. 7:27-16.16(p)2iii] and. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. For the Range III tanks in GR3that are actually used to store gasoline atsome point during the calendar year, theowner or operator shall record the rooflanding emissions for each tank for themonth, the total roof landing emissions forthe month, the sum-to-date of the totalin-service roof landing emissions for themonth and the average-to-date of thein-service roof landing emissions for themonth. [N.J.A.C. 7:27-22.16(o)]None.Page 35 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement44VOC (Total) < 3 tons/yr average fromin-service roof landings (as defined atN.J.A.C. 7:27-16.1) for all tanks storinggasoline in GR3 during the calendar years2017, 2018, and 2019. Applies to tanks E1,E2, E5, E6, E7, E8 and E12. [N.J.A.C.7:27-22.16(a)]VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year. For all Range III tanks inGR3 that are actually used to store gasolineat some point during the calendar year, theowner or operator shall calculate theemissions resulting from in-service rooflandings (as defined at N.J.A.C. 7:27-16.1)each month during operation, using themethodology described in Chapter 7.1.3.2.2of AP-42 (November 2006 or later version)and applying any applicable controlefficiencies. The total sum-to-date shall becalculated by adding the total in-service rooflanding emissions for all tanks in the GR3that are actually used to store gasoline atsome point during the calendar year for themonth to the total in-service roof landingemissions for the previous months duringthe calendar year. The average-to-date shallbe calculated by dividing the totalsum-to-date emissions by the number oftanks in the GR3 that are actually used tostore gasoline at some point during thecalendar year. Any tank in the GR3 thatdoes not store gasoline at some point duringa particular calendar year shall not beincluded when calculating the sums-to-dateor averages-to-date for that year. Thisprocedure will begin in January 2011.[N.J.A.C. 7:27-16.16(p)2iii] and. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. For the Range III tanks in GR3that are actually used to store gasoline atsome point during the calendar year, theowner or operator shall record the rooflanding emissions for each tank for themonth, the total roof landing emissions forthe month, the sum-to-date of the totalin-service roof landing emissions for themonth and the average-to-date of thein-service roof landing emissions for themonth. [N.J.A.C. 7:27-22.16(o)]None.Page 36 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement45VOC (Total) < 2 tons/yr average fromin-service roof landings (as defined atN.J.A.C. 7:27-16.1) for all tanks storinggasoline in GR3 during the calendar years2020 and beyond. Applies to tanks E1, E2,E5, E6, E7, E8 and E12. [N.J.A.C.7:27-22.16(a)]VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year. For all Range III tanks inGR3 that are actually used to store gasolineat some point during the calendar year, theowner or operator shall calculate theemissions resulting from in-service rooflandings (as defined at N.J.A.C. 7:27-16.1)each month during operation, using themethodology described in Chapter 7.1.3.2.2of AP-42 (November 2006 or later version)and applying any applicable controlefficiencies. The total sum-to-date shall becalculated by adding the total in-service rooflanding emissions for all tanks in the GR3that are actually used to store gasoline atsome point during the calendar year for themonth to the total in-service roof landingemissions for the previous months duringthe calendar year. The average-to-date shallbe calculated by dividing the totalsum-to-date emissions by the number oftanks in the GR3 that are actually used tostore gasoline at some point during thecalendar year. Any tank in the GR3 thatdoes not store gasoline at some point duringa particular calendar year shall not beincluded when calculating the sums-to-dateor averages-to-date for that year. Thisprocedure will begin in January 2011.[N.J.A.C. 7:27-16.16(p)2iii] and. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. For the Range III tanks in GR3that are actually used to store gasoline atsome point during the calendar year, theowner or operator shall record the rooflanding emissions for each tank for themonth, the total roof landing emissions forthe month, the sum-to-date of the totalin-service roof landing emissions for themonth and the average-to-date of thein-service roof landing emissions for themonth. [N.J.A.C. 7:27-22.16(o)]None.Page 37 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U12 Tank 105 - Internal Floating Roof Surge Tank with a 26,652 gallon capacity storing petroleum hydrocarbon and VOC liquids.Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1See GR3 for N.J.A.C. 7:27-16.2 applicablerequirements. [N.J.A.C. 7:27-22.16(a)]Other: See GR3 for N.J.A.C. 7:27-16.2monitoring requirements.[N.J.A.C.7:27-22.16(o)].Other: See GR3 for N.J.A.C. 7:27-16.2recordkeeping requirements.[N.J.A.C.7:27-22.16(a)].Demonstrate compliance: As per theapproved schedule. See GR3 for N.J.A.C.7:27-16.2 submittal or action requirements.[N.J.A.C. 7:27-22.16(a)]2Tank contents limited to petroleumhydrocarbon and VOC liquids with a vaporpressure equal to or less than 11.1 psia, thatare not a HAP as defined at 40 CFR63.1(a)(2). Constituent HAPs in gasolineand fuel oils do not have to be speciated.[N.J.A.C. 7:27-22.16(a)]Other: Tank contents shall be monitored byinvoices, delivery receipts or MSDS foreach different product stored.[N.J.A.C.7:27-22.16(o)].Other: The owner or operator shall maintainreadily accessible records showing vaporpressure and description of each productstored.[N.J.A.C. 7:27-22.16(o)].None.3Total Material Transferred <= 960,000gal/yr is the annual total volume limit fromvarious pipeline operations of gasoline andother VOC's in the terminal, based on 36tank turnovers per year. [N.J.A.C.7:27-22.16(e)]Other: Monitored by production recordsbased on tank gauging.[N.J.A.C.7:27-22.16(o)].Total Material Transferred: Recordkeepingby manual logging of parameter or storingdata in a computer data system annually .[N.J.A.C. 7:27-22.16(o)]None.4VOC (Total) <= 0.588 tons/yr. Aannualemission limit from storage, transfer, rooflanding loss, degassing, and cleaning.[N.J.A.C. 7:27-22.16(e)]VOC (Total): Monitored by calculationseach month during operation based onAP-42 (Tanks 3.0 or subsequent version).The owner or operator shall monitor the typematerial stored/transferred including thevapor pressure and description and theamount ofeach material transferred for eachdifferent type of material. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. The owner or operator shallmaintain readily accessible records (seemonitoring requirement) for each differentmaterial stored and transferred and themonthly emission calculations. [N.J.A.C.7:27-22.16(o)]None.5HAPs (Total): All HAP emissions are belowreporting threshold from operating permitrenewal application. [N.J.A.C.7:27-22.16(a)]HAPs (Total): Monitored by calculationseach month during operation based onAP-42 (Tanks 3.0 or subsequent version).The owner or operator shall monitor the typematerial stored/transferred including thevapor pressure and description and theamount ofeach material transferred for eachdifferent type of material. [N.J.A.C.7:27-22.16(o)]HAPs (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. The owner or operator shallmaintain readily accessible records (seemonitoring requirement) for each differentmaterial stored and transferred and themonthly emission calculations. [N.J.A.C.7:27-22.16(o)]None.OS SummaryPage 38 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6All requests, reports, applications,submittals, and other communications to theAdministrator pursuant to Part 60 shall besubmitted in duplicate to the RegionalOffice of US Environmental ProtectionAgency. Submit Region II infromation to:Director, Air and Waste ManagementDivision, US Environmental ProtectionAgency, Federal Office Building, 26 FederalPlaza, New York, NY10278.[40 CFR60.4(a)]None.None.Submit a report: As per the approvedschedule to EPA as per regulation by 40CFR 60. [40 CFR 60.4(a)]7Copies of all information submitted to theEPA pursuant to 40 CFR Part 60, shall alsobe submitted to NJDEP RegionalEnforcement Office. [40 CFR 60.4(b)]None.None.Submit a report: As per the approvedschedule as regulated by 40 CFR 60. [40CFR 60.4(b)]8The owner or operator subject to theprovisions of 40 CFR Part 60 shall furnishthe Administrator written notification of anyphysical or operational change to an existingfacility which may increase the emission rateof any air pollutant to which a standardapplies. The notification shall includeinformation describing the precise nature ofthe change, present and proposed emissioncontrol systems, productive capacity offacility before and after the change and theexpected completion date of the change.Notification shall be postmarked within 60days or soon as practicable before anychange is commenced.[40 CFR 60.7(a)(4)]None.None.Submit notification: As per the approvedschedule to EPA Region II and RegionalEnforcement Office. [40 CFR 60.7(a)(4)]Page 39 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9At all times, including periods of start-up,shutdown, and malfunction, owners andoperators shall, to the extent practicable,maintain and operate any affected facilityincluding associated air pollution controlequipment in a manner consistent with goodair pollution control practice for minimizingemissions. Determination of whetheracceptable operating and maintenanceprocedures are being used will be based oninformation available to the Administratorwhich may include, but is not limited to,monitoring results, opacity observations,review of operation and maintenanceprocedures, and inspection of the source.[40 CFR 60.11(d)]None.None.None.10No owner or operator subject to NSPSstandards in Part 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to theatmosphere.[40 CFR 60.12]None.None.None.Page 40 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement11The owner or operator of each storage vesselwith a design capacity greater than or equalto 19,812 gallons but less than 39,889gallons containing a VOL that, as stored,has a maximum true vapor pressure equal toor greater than 4.00 psia but less than 11.1psia, shall equip each storage vessel with afixed roof in combination with an internalfloating roof.(i) The internal floating roof shall rest orfloat on the liquid surface (but notnecessarily in complete contact with it)inside a storage vessel that has a fixed roof.The internal floating roof shall be floatingon the liquid surface at all times, exceptduring initial fill and during those intervalswhen the storage vessel is completelyemptied or subsequently emptied andrefilled. When the roof is resting on the legsupports, the process of filling, emptying, orrefilling shall be continuous and shall beaccomplished as rapidly as possible.(ii) The internal floating roof shall beequipped with mechanical shoe seal betweenthe wall of the storage vessel and the edge ofthe internal floating roof. A mechanicalshoe seal is a metal sheet held verticallyagainst the wall of the storage vessel bysprings or weighted levers and is connectedby braces to the floating roof. A flexiblecoated fabric (envelope) spans the annularspace between the metal sheet and thefloating roof. [40 CFR 60.12b(a)(1)]Monitored by visual determination uponinstallation of the control device, prior tofilling. The owner or operator shall visuallyinspect the internal floating roof, theprimary seal, and the secondary seal (if oneis in service), priorto filling the storagevessel with VOL. If there are holes, tears, orother openings in the primary seal, thesecondary seal, or the seal fabric or defectsin the internal floating roof, or both, theowner or operator shall repair the itemsbefore filling the storage vessel.. [40 CFR 60.113b(a)(1)]Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon installation of the controldevice, prior to filling The owner oroperator shall keep a record of eachinspection performed as required by 40 CFR60.113b(a)(1), (a)(2) and (a)(4) for at leasttwo years. Each record shall identify thestorage vessel on which the inspection wasperformed and shall contain the date thevessel was inspected and the observedcondition of each component of the controlequipment (seals, internal floating roof, andfittings). [40 CFR 60.115b(a)(2)]Submit notification: As per the approvedschedule. The owner or operator shallnotify the Administrator in writing at least30 days prior to the filling or refilling ofeach storage vessel for which an inspectionis required by 40 CFR 60.113b(a)(1) and(a)(4) to afford the Administrator theopportunity to have an observer present. Ifthe inspection required by 40 CFR60.113b(a)(4) is not planned and the owneror operator could not have known about theinspection 30 days in advance or refillingthe tank, the owner or operator shall notifythe Administrator at least 7 days prior to therefilling of the storage vessel. Notificationshall be made by telephone immediatelyfollowed by written documentationdemonstrating why the inspection wasunplanned. Alternatively, this notificationincluding the written documentation may bemade in writing and sent by express mail sothat it is received by the Administrator atleast 7 days prior to the refilling.In addition, the owner or operator shallfurnish the Administrator with a report thatdescribes the control equipment and certifiesthat the control equipment meets thespecifications of 40 CFR 60.112b(a)(1) and113b(a)(1). This report shall be anattachment to the notification required by 40CFR 60.7(a)(3). [40 CFR 60.113b(a)(5)]and. [40 CFR 60.115b(a)(1)]Page 41 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1240 CFR 60.112b(a)(1) continued:(iii) Each opening in a noncontact internalfloating roof except for automatic bleedervents (vacuum breaker vents) and the rimspace vents is to provide a projection belowthe liquid surface.(iv) Each opening in the internal floatingroof except for leg sleeves, automaticbleeder vents, rim space vents, columnwells, ladder wells, sample wells, and stubdrains is to be equipped with a cover or lidwhich is to be maintained in a closedposition at all times (i.e., no visible gap)except when the device is in actual use. Thecover or lid shall be equipped with a gasket.Covers on each access hatch and automaticgauge float well shall be bolted except whenthey are in use.(v) Automatic bleeder vents shall beequipped with a gasket and are to be closedat all times when the roof is floating exceptwhen the roof is being floated off or is beinglanded on the roof leg supports.(vi) Rim space vents shall be equipped witha gasket and are to be set to open only whenthe internal floating roof is not floating or atthe manufacturer's recommended setting.(vii) Each penetration of the internal floatingroof for the purpose of sampling shall be asample well. The sample well shall have aslit fabric cover that covers at least 90percent of the opening. [40 CFR60.12b(a)(1)]Monitored by visual determination annually.The owner or operator shall visually inspectthe internal floating roof and the primaryseal or the secondary seal (if one is inservice) through manholes and roof hatcheson the fixed roof at least once every 12months after initial fill. If the internalfloating roof is not resting on the surface ofthe VOL inside the storage vessel, or there isliquid accumulated on the roof, or the seal isdetached, or there are holes or tears in theseal fabric, the owner or operator shallrepair the items or empty and remove thestorage vessel from service within 45 days.If a failure that is detected duringinspections required in this paragraphcannot be repaired within 45 days and if thevessel cannot be emptied within 45 days, a30-day extension may be requested from theAdministrator in the inspection reportrequired in 40 CFR 60.115b(a)(3). Such arequest for an extension must document thatalternate storage capacity is unavailable andspecify a schedule of actions the companywill take that will assure that the controlequipment will be repaired or the vessel willbe emptied as soon as possible. [40 CFR60.113b(a)(2)]Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually. The owner or operatorshall keep a record of each inspectionperformed as required by 40 CFR60.113b(a)(1), (a)(2) and (a)(4) for at leasttwo years. Each record shall identify thestorage vessel on which the inspection wasperformed and shall contain the date thevessel was inspected and the observedcondition of each component of the controlequipment (seals, internal floating roof, andfittings). [40 CFR 60.115b(a)(2)]Submit a report: Upon occurrence of event.The owner or operator shall furnish a reportto the Administrator within 30 days of theannual inspection required by 40 CFR60.113b(a)(2), if any of the conditionsdescribed in 40 CFR 60.113b(a)(2) aredetected during the visual inspection. Eachreport shall identify the storage vessel, thenature of the defects, and the date thestorage vessel was emptied or the nature ofand date the repair was made. [40 CFR60.115b(a)(3)]Page 42 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U15 Marine Loading of petroleum hydrocarbon liquids (treated as gasoline) and VOC liquids (applicable and non-applicable)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1VOC (Total) <= 27.05 tons any consecutive12-month period . Maximum annualemission limit from operating permitmodification application. [N.J.A.C.7:27-22.16(a)]Other: The owner or operator shall monitorthe amount of material loaded, the type ofmaterial (description including vaporpressure) and the date of the loading foreach material loaded in OS1 and OS2. Theemissions from each loading and amonth-to-date shall be calculated.[N.J.A.C.7:27-22.16(o)].VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. The owner or operator shallrecord the monitored parameters and theemissions per any consecutive 12-monthperiod. The emissions per any consecutive12-month period shall be calculated by thesum of the emissions calculated during anyone month added to the sum of theemissions calculated during the preceding11 months. The owner or operator shallstart this procedure starting with the first fullmonth after the approval of BOP060001.[N.J.A.C. 7:27-22.16(o)]None.2Benzene <= 0.243 tons any consecutive12-month period . Maximum annualemisison limit from operating permitmodification application based on EPAHAP to VOC percentage guidelines.[N.J.A.C. 7:27-22.16(a)]Other: The owner or operator shall monitorthe amount of material loaded, the type ofmaterial (description including vaporpressure) and the date of the loading foreach material loaded in OS1 and OS2. Theemissions from each loading and amonth-to-date shall be calculated.[N.J.A.C.7:27-22.16(o)].Benzene: Recordkeeping by manual loggingof parameter or storing data in a computerdata system each month during operation.The owner or operator shall record themonitored parameters and the emissions perany consecutive 12-month period. Theemissions per any consecutive 12-monthperiod shall be calculated by the sum of theemissions calculated during any one monthadded to the sum of the emissions calculatedduring the preceding 11 months. The owneror operator shall start this procedure startingwith the first full month after the approval ofBOP060001. [N.J.A.C. 7:27-22.16(o)]None.OS SummaryPage 43 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3Conduct a comprehensive stack test atemission point PT15 at least 18 monthsprior to the expiration date of the approvedOperating Permit to demonstrate compliancewith the VOC emission limit of tenmilligrams per liter of gasoline loaded, lb/hrand control efficiency. The test and shall beperformed for at least 60 minutes during thetransfer of the last 50 percent of total liquidcargo. For a transfer operation for which thetransfer of the last 50 percent of the totalliquid cargo is less than a 60 minuteduration, the testing shall be performedduring the transfer of the entire last 50percent of the total liquid cargo.Testing must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable emissionstandards, but without creating an unsafecondition.The initial stack test shall satisfy thisrequirement for the first term of theoperating permit (9/29/03 to 9/28/08).[N.J.A.C. 7:27-16.5(h)] and. [N.J.A.C.7:27-22.16(a)]Monitored by stack emission testing prior topermit renewal. Unless otherwise approvedin the stack test protocol or by theDepartment, each test run shall be60-minutes in sampling duration. [N.J.A.C.7:27-22.16(o)]Recordkeeping by stack test results every 5years . [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Submit a stack test protocol to theBureau of Technical Services (BTS) at P.O.Box 437, Trenton, NJ 08625 at least 30months prior to the expiration of theapproved operating permit. Within 30 daysof protocol approval, the permittee shallcontact the Bureau of Technical Services at(609) 530-4041 to schedule a mutuallyacceptable test date. The stack test must beconducted during the Ozone Season (May 1through September 30) . The stack testreport must be submitted to BTS within 45days after performing the stack test pursuantto N.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of the test results must be submittedwith the operating permit renewalapplication due at least 12 months prior toexpiration of the Operating Permit.Test results shallreport VOC in lb/hr,mg/liter product loaded and controlefficiency. [N.J..AC. 7:27-22.18(e)] and.[N.J.A.C. 7:27-22.18(h)]Page 44 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4Conduct a comprehensive stack test atemission point PT15 to demonstratecompliance with the VOC emission limit often milligrams per liter of gasoline loaded,lb/hr and control efficiency. The test shall beperformed for at least 60 minutes during thetransfer of the last 50 percent of total liquidcargo. For a transfer operation for which thetransfer of the last 50 percent of the totalliquid cargo is less than a 60 minuteduration, the testing shall be performedduring the transfer of the entire last 50percent of the total liquid cargo.Testing must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable emissionstandards, but without creating an unsafecondition. [N.J.A.C. 7:27-16.5(h)] and.[N.J.A.C. 7:27-22.16(a)]Monitored by stack emission testing onceinitially. Unless otherwise approved in thestack test protocol or by the Department,each test run shall be 60-minutes insampling duration. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by stack test results onceinitially. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Submit a stack test protocol to theBureau of Technical Services (BTS) at P.O.Box 437, Trenton, NJ 08625 within 30 daysfrom the date of the approved operatingpermit (BOP060001). Within 30 days ofprotocol approval, the permittee shallcontact the Bureau of Technical Services at(609) 530-4041 to schedule a mutuallyacceptable test date. The stack test must beconducted by Deember 31, 2008. The stacktest report must be submitted to BTS within45 days after performing the stack testpursuant to N.J.A.C. 7:27-22.19(d). Thetest results must be certified by a New Jerseylicensed professional engineer or certifiedindustrial hygienist.A copy of the test results must be submittedwith the operating permit renewalapplication due at least 12 months prior toexpiration of the Operating Permit.Test results shallreport VOC in lb/hr,mg/liter product loaded and controlefficiency. [N.J.A.C. 7:27-22.18(e)] and.[N.J.A.C. 7:27-22.18(h)]Page 45 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U15 Marine Loading of petroleum hydrocarbon liquids (treated as gasoline) and VOC liquids (applicable and non-applicable)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1VOC Control Efficiency >= 95 % by weight.The owner or operator shall install andoperate a control apparatus, which reducesthe total VOC emissions to the outdooratmosphere resulting from gasoline andapplicable VOC transfers at the facility byno less than the specified amount.[N.J.A.C.7:27-16.5(b)] and. [N.J.A.C.7:27-16.5(c)]VOC Control Efficiency: Monitored bystack emission testing once initially andprior to permit renewal, based on each ofthree Department validated stack test runs.See stack test details in the OS Summary.[N.J.A.C. 7:27-22.16(o)]VOC Control Efficiency: Recordkeeping bystack test results once initially and prior topermit renewal. See stack test details in theOS Summary. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in the OSSummary. [N.J.A.C. 7:27-22.16(o)]2The vapor recovery unit shall be used duringall periods of ballasting. [N.J.A.C.7:27-16.5(e)2]None.None.None.3The permittee shall not cause, suffer orallow the transfer of any applicable VOC orballasting if the delivery vessel beingloaded, any control apparatus, or otherequipment serving the transfer has a leakwhich results in a concentration of VOCgreater than or equal to 100% of the LEL ofpropane when measured at a distance of 1inch (1") or less from the source. [N.J.A.C.7:27-16.5(f)1i]Monitored by visual determination uponoccurrence of event. The permittee shallinspect the transfer marine tank vessel,delivery vessel and control apparatus forleaks prior to beginning and during thetransfer. Upon detection of a leak thepermittee has the option of verification ofthe leak with a portable instrumentaccording to EPA's Reference Method 21(40 CFR Part 60 Appendix A) ordiscontinuing the loading operation until theleak is repaired. [N.J.A.C. 7:27-16.5(g)]Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event (parameter= test results). [N.J.A.C. 7:27-22.16(o)]None.4The permittee shall not cause, suffer, allowor permit the transfer of any applicable VOCor ballasting if the delivery vessel beingloaded, any control apparatus, or otherequipment serving the transfer has a liquidleak of applicable VOC. [N.J.A.C.7:27-16.5(f)1ii]Other: The permittee shall inspect thetransfer marine tank vessel, delivery vesseland control apparatus for liquid leaks byvisual determination prior to beginning andduring transfer.[N.J.A.C. 7:27-22.16(o)].Other: Maintain readily accessible recordsof inspections.[N.J.A.C. 7:27-22.16(o)].None.5The permittee shall not cause, suffer, allowor permit the transfer of any applicable VOCor ballasting if any component of the marinetank vessel or any control apparatus servingthe source operation is not installed andoperating as designed. [N.J.A.C.7:27-16.5(f)2]Other: The permittee shall conduct a visualinspection of the transfer marine tank vessel,delivery vessel and control apparatus priorto beginning transfer.[N.J.A.C.7:27-22.16(o)].Other: Maintain readily accessible recordsof inspections.[N.J.A.C. 7:27-22.16(o)].None.OS1 Loading of Petroleum Hydrocarbon and VOC liquids (vp <= 11.1 psia) with carbon adsorber (CD1)Page 46 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6VOC (Total): The permittee shall not cause,suffer, allow or permit the transfer of anyapplicable VOC or ballasting if the transferresults or would result in a liquid VOC spill.[N.J.A.C. 7:27-16.5(f)3]Other: The permittee shall conduct a visualinspection of the transfer marine tank vessel,delivery vessel and control apparatus priorto beginning and during transfer.[N.J.A.C.7:27-22.16(o)].Other: Maintain readily accessible recordsof inspections.[N.J.A.C. 7:27-22.16(o)].None.7The owner or operator of a marine terminalshall maintain at the marine terminal recordssufficient to demonstrate compliance withN.J.A.C. 7:27-16.5. Any records required bythis section shall be made available to theDepartment upon request and shall bemaintained for five years. [N.J.A.C.7:27-16.5(j) &. [N.J.A.C. 7:27-16.22(a)]None.Other: For each transfer of gasoline or otherapplicable VOC to the marine tank vesseland for performance of ballasting on amarine tank vessel at the marine terminal,the records shall include the followinginformation:1. The company name and address of themarine terminal;2. The date;3. The name and registry of the marinetank vessel;4. For any transfer operation, the type ofVOC and the quantity, in gallons or liters,loaded into the marine tank vessel;5. The prior cargo carried by the marinetank vessel and the condition (that is,cleaned, crude oil washed, gas freed, etc.) ofthe cargo tanks on the marine tank vesselprior to their being loaded or ballasted; and6. For ballasting, the amount of ballastwater or other liquid added to ballast tankswhich are unsegregated and which maycontain VOC vapor.[N.J.A.C. 7:27-16.5(j)].None.8Tank contents limited to petroleumhydrocarbon and VOC liquids with a vaporpressure equal to or less than 11.1 psia, thatare not a HAP as defined at 40 CFR63.1(a)(2). Constituent HAPs in gasolineand fuel oils do not have to be speciated.[N.J.A.C. 7:27-22.16(a)]Other: Monitored by marine loading recordseach loading.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event. Recordthe description, vapor pressure and dateloaded for each product loaded. [N.J.A.C.7:27-22.16(o)]None.9Total Material Transferred <= 420,000gal/hr from operating permit modicationapplication. [N.J.A.C. 7:27-22.16(a)]Other: Maximum design capacity for carbonadsorption system.[N.J.A.C. 7:27-22.16(o)].Other: Maintain readily accessible designrecords of the carbon adsorptionsystem.[N.J.A.C. 7:27-22.16(o)].None.10VOC (Total) <= 35.02 lb/hr. Maximumemission rate from the Carbon Adsorptionsystem from the operating permitmodification application. [N.J.A.C.7:27-22.16(a)]VOC (Total): Monitored by stack emissiontesting once initially and prior to permitrenewal, based on each of three Departmentvalidated stack test runs. See stack testdetails in the OS Summary. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults once initially and prior to permitrenewal. See stack test details in the OSSummary. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in the OSSummary. [N.J.A.C. 7:27-22.16(o)]Page 47 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement11VOC (Total) <= 6,200 ppmv expressed aspropane base on a 6 hour rolling averagebased on 1 hour blocks. [N.J.A.C.7:27-22.16(a)]VOC (Total): Monitored by continuousemission monitoring system continuously,based on 1 minute intervals used to calculate1 hour block averages. [N.J.A.C.7:27-22.16(o)]VOC (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. THC emission shallbe recorded for each 6-hour rolling blockperiod, based on 60 minute blocks.[N.J.A.C. 7:27-22.16(o)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(o)]12THC <= 10 mg/liter gasoline loaded.Maximum THC stack concentration fromthe operating permit modificaitonapplication. [N.J.A.C. 7:27-22.16(a)]THC: Monitored by stack emission testingonce initially and prior to permit renewal,based on each of three Department validatedstack test runs. See stack test test detail inthe OS Summary. [N.J.A.C. 7:27-22.16(o)]THC: Recordkeeping by stack test resultsonce initially and prior to permit renewal.See stack test test detail in the OS Summary.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test test detail in the OSSummary. [N.J.A.C. 7:27-22.16(o)]13All air-contaminant emissions from loadingof gasoline and applicable VOC as cargo onmarine tank vessels shall be directed to thecarbon adsorption system. [N.J.A.C.7:27-22.16(a)]None.None.None.14Spent carbon shall be disposed inaccordance with all state and federalregulations. [N.J.A.C. 7:27-22.16(e)]None.Recordkeeping by manual logging ofparameter upon occurrence of event.Maintain records indicating the date andlocation of spent carbon disposition.[N.J.A.C. 7:27-22.16(o)]None.Page 48 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15The owner or operator shall develop aQA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)]Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis.[N.J.A.C. 7:27-22.16(o)].Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports.[N.J.A.C. 7:27-22.16(o)].Submit a report: Every April 30, July 30,October 30, and January 30 for thepreceding quarter year (the quarter yearsbegin on January 1, April 1, July 1, andOctober 1). All quarterly and annual QAdata shall be included in quarterly EEMPRreports and kept on file at the facility. TheQA data must be made available to theDepartment upon request.. [N.J.A.C. 7:27-22.16(o)]16The recordkeeping requirements of 40 CFR63.567(j)(4) and the emission estimationrequirements of 40 CFR 63.565(l) apply toexisting sources with emissions less than 10and 25 tons. [40 CFR 63.560(a)(3)]Monitored by calculations annually. Theowner or operator shall calculate an annualestimate of HAP emissions, excludingcommodities exempted by 40 CFR63.560(d), from marine tank vessel loadingoperations. Emission estimates and emissionfactors shall be based on test data, or if testdata is not available, shall be based onmeasurement or estimating techniquesgenerally accepted in industry practice foroperating conditions at the source. [40 CFR63.565(l)]Other: The owner and operator of marinetank vessel loading operations specified in40 CFR 63.560(a)(3) shall retain records ofthe emissions estimates determined in 40CFR 65.565(l) and records of their actualthroughputs by commodity for 5 years.[40CFR 63.567(j)(4)].None.Page 49 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U15 Marine Loading of petroleum hydrocarbon liquids (treated as gasoline) and VOC liquids (applicable and non-applicable)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1VOC (Total) <= 6.72 lb/hr. Maximumhourly emission rate from operating permitmodification application. [N.J.A.C.7:27-22.16(e)]VOC (Total): Monitored by calculationsonce initially. [N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system once initially.[N.J.A.C. 7:27-22.16(o)]None.2Total Material Transferred <= 504,000gal/hr. Maximum hourly transfer limit onloading of non-applciable VOC liquidsincluding distillate fuel oil from operatingpermit modification application. [N.J.A.C.7:27-22.16(a)]None.None.None.3Loading limited to any petroleumhydrocarbon liquid, that is not a HAP asdefined at 40 CFR 63.1(a)(2), with a vaporpressure less than 0.02 psia at standardsconditions into non-gasoline vapor ladenmarine vessels. Constituent HAPs in fueloils do not have to be speciated. [N.J.A.C.7:27-22.16(a)]Other: Monitor by reviewing marine loadingrecords each loading.[N.J.A.C.7:27-22.16(o)].Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event. Recordthe description, vapor pressure and date loadfor each product loaded. [N.J.A.C.7:27-22.16(o)]None.OS2 Loading of VOC liquids (vp < 0.02 psia) without control devicePage 50 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U40 Two Boilers, each 29.3 MM BTU/hr. firing No. 6 fuel oilOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1No person shall cause, suffer, allow orpermit visible smoke to be emitted into theoutdoor air from the combustion of fuel inany stationary indirect heat exchangeremissions except for a period of not longerthan three minutes in any consecutive30-minute period. [N.J.A.C. 7:27-3.2(a)]and. [N.J.A.C. 7:27- 3.2(c)]Monitored by visual determination daily,based on an instantaneous determination.For compliance with the opacity standard,the owner or operator shall conduct visualopacity inspections during daylight hours.Visual inspections shall consist of a visualsurvey to identify if the stack has visibleemissions, (other than condensed watervapor), greater than the prescribed standard.If visible emissions are observed, thepermittee shall do the following: (1) Verifythat the equipment and/or control devicecausing the emission is operating accordingto manufacturer's spedifications and theoperating permit compliance plan. If theequipment or control device is not operatingproperly, the permittee shall take correctiveaction immediately to eliminate the excessemissions. The permittee must report anypermit violation to NJDEP pursuant toN.J.A.C. 7:27-22.19. (2) If the correctiveaction taken in step one does not correct theopacity problem within 24 hours, thepermittee shall perform a check via acertified opacity reader, in accordance withN.J.A.C. 7:27B-2. Such a test shall beconducted once per day until correctiveaction is taken to successfully correct theopacity problem. The permittee must reportany continuing permit violation to NJDEPpursuant to N.J.A.C. 7:27-22.19. [N.J.A.C.7:27-22.16(o)]Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. The owner or operator shallrecord and retain the following records daily.(1) Date and time of inspection;(2) Emission Point number;(3) Operational status of equipment;(4) Observed results and conclusions;(5) Description of corrective action taken ifneeded;(6) Date and time opacity problem wassolved, if applicable;(7) N.J.A.C. 7:27B-2 results if conducted;and(8) Name of person(s) conductinginspection. [N.J.A.C. 7:27-22.16(o)]None.2Particulate Emissions <= 8.09 lb/hr.Particulate emission limit from thecombustion of fuel based on rated heat inputfor each boiler. [N.J.A.C. 7:27- 4.2(a)]None.None.None.3Maximum allowable sulfur content in fueloil by fuel oil type/viscosity andgeographical zone is 0.3 percent sulfur byweight. [N.J.A.C. 7:27- 9.2(b)]Monitored by review of fuel deliveryrecords per delivery showing sulfur content.[N.J.A.C. 7:27-22.16(o)]Recordkeeping by fuel certification receiptsper delivery. Keep certificate of analysisshowing fuel sulfur content. [N.J.A.C.7:27-22.16(o)]None.OS SummaryPage 51 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4Maximum allowable sulfur content in fueloil by fuel oil type/viscosity andgeographical zone is 0.3 percent Sulfur byweight. [N.J.A.C. 7:27- 9.2(b)]Monitored by fuel sampling (e.g. oil) eachmonth during operation. The owner oroperator shall collect an oil sample fromeach fuel tank. A composite of the 12monthly samples shall be analyzed once peryear to determine sulfur content. [N.J.A.C.7:27-22.16(o)]Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually. The owner or operatorshall maintain readily accessible records ofthe sulfur content analysis. [N.J.A.C.7:27-22.16(o)]None.Page 52 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Adjust the combustion process annually inaccordance with the procedure set forth atN.J.A.C. 7:27-19.16 in the same quarter ofeach calendar year beginning. [N.J.A.C.7:27-16.8(c)3i] and. [N.J.A.C.7:27-19.7(a)1]Monitored by periodic emission monitoringannually The owner or operator shall:1. Inspect the burner, and clean or replaceany components of the burner as necessary;2. Inspect the flame pattern and make anyadjustments to the burner necessary tooptimize the flame pattern consistent withthe manufacturer's specifications;3. Inspect the system controlling theair-to-fuel ratio, and ensure that it iscorrectly calibrated and functioning properly;4. Minimize total emissions of NOx and COconsistent with the manufacturer'sspecifications;5. Measure the concentrations in the effluentstream of NOx, CO and O2 in ppmvd,before and after the adjustment is made; and6. Convert the emission values of the NOx,CO and O2 concentrations measuredpursuant to (a)5 above to pounds per millionBTU (lb/MM BTU) according to thefollowing formula:lb/MM BTU = ppmvd x MW x F dry factorx O2 correction factor ? 387,000,000Where:ppmvd is the concentration in parts permillion by volume, dry basis, of NOx or COMW is the Molecular Weight for: NOx = 46lb/lb-mole; CO = 28 lb/lb-moleF dry factor for:Natural gas = 8,710 dscf/MM BTUResidual or fuel oil = 9,190 dscf/MM BTUO2 correction factor: (20.9%) ? (20.9% - O2measured). O2 measured is percent oxygenon a dry basis. [N.J.A.C. 7:27-16.8],[N.J.A.C. 7:27-19.7] and. [N.J.A.C.7:27-19.16(a)]Other: The owner or operator of theequipment or source operation adjusted shallensure that each adjustment is recorded in alog book or computer data system andretained for a minimum of five years, to bemade readily accessible to the Departmentupon request. Such record shall contain thefollowing information for each adjustment:1. The date of the adjustment and the timesat which it began and ended,2. The name, title and affiliation of theperson whom made the adjustment,3. The NOx and CO concentrations in theeffluent stream, in ppmvd, before and aftereach actual adjustment was made,4. The concentration of O2 (in percent drybasis) at which the CO and NOxconcentrations were measured;5. A description of any corrective actiontaken;6. results from any subsequent testperformed after taking any corrective action,including concentrations and convertedemission values in pounds per million BTU(lb/MM BTU);7. The type and amount of fuel used over the12 months prior to the annual adjustment;and8. Any other information which theDepartment or the EPA has required as acondition of approval of any permit orcertificate issued for the equipment orsource operation.The records must be kept annually.[N.J.A.C.7:27-19.16].Submit a report: As per the approvedschedule. The owner or operator shallensure that an annual adjustmentcombustion processreport is submittedelectronically to the Department (RegionalEnforcement Office listed on first page ofOperating Permit) within 45 days after theadjustment of the combustion process iscompleted, based on the gross heat input ofthe boiler, beginning in 2009 in the formatthe Department specifies at its website. Thereport shall contain the followinginformation:1.The concentration of NOx and CO in theeffluent stream in ppmvd, and O2; inpercent dry basis, measured before and afterthe adjustment of the combustion process;2. The converted emission values inlb/MMBTU for the measurements takenbefore and after the adjustment of thecombustion process;3. A description of any corrective actiontaken as part of the combustion adjustment;and4. The type and amount of fuel used over the12 months prior to the annual adjustment.[N.J.A.C. 7:27-19.16]Page 53 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6The owner or operator of the adjustedequipment or source operation shall ensurethat the operating parameter settings areestablished and recorded after thecombustion process is adjusted and that theadjusted equipment or source operation ismaintained to operate consistent with theannual adjustment. [N.J.A.C. 7:27-19.16(e)]Other: Monitor and maintain the operatingparameter settings that are established afterthe combustion process is adjusted in orderto operate consistent with the annualadjustment.[N.J.A.C. 7:27-22.16(o)].Other: The owner or operator shall recordthe operating parameter settings that areestablished after the combustion process isadjusted.[N.J.A.C. 7:27-19.16(e)].None.7NOx (Total) <= 23.7 tons/yr. Annualemission limit for both boilers based annualfuel usage from operating permitmodification application. [N.J.A.C.7:27-22.16(a)]None.None.None.8CO <= 0.104 tons/yr. Annual emission limitfor boiler #1 based annual fuel usage fromoperating permit modification application.(Emissions for boiler #2 are below reportingthreshold). [N.J.A.C. 7:27-22.16(a)]None.None.None.9SO2 <= 14.1 tons/yr. Annual emission limitfor both boilers based annual fuel usagefrom operating permit modificationapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.10TSP <= 1.88 tons/yr. Annual emission limitfor both boilers based annual fuel usagefrom operating permit modificationapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.11PM-10 (Total) <= 1.88 tons/yr. Annualemission limit for both boilers based annualfuel usage from operating permitmodification application. [N.J.A.C.7:27-22.16(a)]None.None.None.12Maximum Gross Heat Input <= 29.3MMBTU/hr (HHV). Maximum gross heatinput ofeach boiler based on higher heating(HHV) value of fuel from operating permitmodification application. [N.J.A.C.7:27-22.16(a)]Other: Fuel Burner RatedCapacity.[N.J.A.C. 7:27-22.16(o)].None.None.Page 54 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement13Fuel Oil Usage <= 600,000 gallons per anyconsecutive 12 month period, fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]Fuel Oil Usage: Monitored by fuel usagetotalizing meter continuously. [N.J.A.C.7:27-22.16(o)]Fuel Oil Usage: Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. The owner or operator shall thefuel usage each month. Gallons perconsecutive 12-month period shall becalculated by the sum of the gallonsconsumed during any one month added tothe sum of the gallons consumed during thepreceding 11 months. This procedure willbegin with the first full month following thefinal issuance of the operating permit. Thisaccounting will not include oil consumptionduring months prior to the approval of theOperating permit. The permittee will selectthe time period for accounting, such as fiscalmonth, calendar month or productionmonth. Once selected, the period must notbe changed without prior approval fromNJDEP. [N.J.A.C. 7:27-22.16(o)]None.14Fuel usage limited to #6 fuel oil fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]None.None.None.Page 55 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15Conduct a comprehensive stack test atemission point PT13 and PT14 at least 18months prior to the expiration date of theapproved Operating Permit to demonstratecompliance with the CO, NOx and TSPemission limits, while firing No. 6 fuel oil.The test shall be conducted at 95% to 100%of rated capacity. [N.J.A.C. 7:27-22.16(a)]Monitored by stack emission testing prior topermit renewal. Unless otherwise approvedin the stack test protocol or by theDepartment, each test run shall be60-minutes in sampling duration. [N.J.A.C.7:27-22.16(o)]Recordkeeping by stack test results prior topermit renewal . [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Submit a stack test protocol to theBureau of Technical Services (BTS) at P.O.Box 437, Trenton, NJ 08625 at least 30months prior to the expiration of theapproved operating permit. Within 30 daysof protocol approval, the permittee shallcontact the Bureau of Technical Services at(609) 530-4041 to schedule a mutuallyacceptable test date. The stack test must beconducted during January, February,November or December. The stack testreport must be submitted to BTS within 45days after performing the stack test pursuantto N.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of the test results must be submittedwith the operating permit renewalapplication due at least 12 months prior toexpiration of the Operating Permit.Test results shall report lb/hr. [N.J..AC.7:27-22.18(e)] and. [N.J.A.C.7:27-22.18(h)]Page 56 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement16Conduct a comprehensive stack test atemission point PT13 to demonstratecompliance with the CO, NOx and TSPemission limits, while firing No. 6 fuel oil.The test shall be conducted at 95% to 100%of rated capacity. [N.J.A.C. 7:27-22.16(a)]. Unless otherwise approved in the stacktest protocol or by the Department, each testrun shall be 60-minutes in samplingduration. Monitored by stack emissiontesting once initially. [N.J.A.C.7:27-22.16(o)]Recordkeeping by stack test results onceinitially. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Submit a stack test protocol to theBureau of Technical Services (BTS) at POBox 437, Trenton, NJ 08625 within 60 daysfrom the date of the approved operatingpermit modification (BOP080001). Within30 days of protocol approval, the permitteemust contact BTS at 609-530-4041 toschedule a mutually acceptable test date.The stack test must be conducted within 180days from the date of the approved operatingpermit modifications (BOP080001). Thestack test report must be submitted to BTSwithin 45 days after performing the stacktest pursuant to N.J.A.C. 7:27-22.19(d). Thetest results must be certified by a New Jerseylicensed professional engineer or certifiedindustrial hygienist.A copy of the test results must be submittedwith the operating permit renewalapplication due at least 12 months prior toexpiration of the Operating Permit.Test results shall report lbs/hour. [N.J.A.C.7:27-22.18(e)] and. [N.J.A.C.7:27-22.18(h)]Page 57 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U40 Two Boilers, each 29.3 MM BTU/hr. firing No. 6 fuel oilOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1NOx (Total) <= 13.1 lb/hr. Maximumemission rate based on maximum gross heatinput to the boiler when firing No. 6 fuel oilfrom operating permit modificationapplication. [N.J.A.C. 7:27-22.16(a)]NOx (Total): Monitored by stack emissiontesting once initially and prior to permitrenewal, based on each of three Departmentvalidated stack test runs. See stack testdetails in OS Summary. [N.J.A.C.7:27-22.16(o)]NOx (Total): Recordkeeping by stack testresults once initially and prior to permitrenewal. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]2CO <= 0.058 lb/hr. Maximum emission ratebased on maximum gross heat input to theboiler when firing No. 6 fuel oil fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]CO: Monitored by stack emission testingonce initially and prior to permit renewal,based on each of three Department validatedstack test runs. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]CO: Recordkeeping by stack test resultsonce initially and prior to permit renewal.See stack test details in OS Summary.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]3SO2 <= 7.82 lb/hr. Maximum emission ratebased on maximum gross heat input to theboiler when firing No. 6 fuel oil fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]None.None.None.4TSP <= 0.691 lb/hr. Maximum emissionrate based on maximum gross heat input tothe boiler when firing No. 6 fuel oil fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]TSP: Monitored by stack emission testingonce initially and prior to permit renewal,based on each of three Department validatedstack test runs. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]TSP: Recordkeeping by stack test resultsonce initially and prior to permit renewal.See stack test details in OS Summary.[N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]5PM-10 (Total) <= 0.691 lb/hr. Maximumemission rate based on maximum gross heatinput to the boiler when firing No. 6 fuel oilfrom operating permit modificationapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.6Maximum Gross Heat Input <= 24.9MMBTU/hr (HHV). Maximum heat inputrate based on 178 gallons per hour fuel oilusage from operating permit minormodification, BOP080001. [N.J.A.C.7:27-22.16(a)]Maximum Gross Heat Input: Monitored byfuel flow/firing rate instrumentcontinuously, based on a 1 hour blockaverage. The owner or operator shall installand operate a fuel flowmeter that shall meetan accuracy of not less than 2% per 40 CFR75, Appendix D. The fuel limit shall be <=178 gallon of fuel oil per hour. [N.J.A.C.7:27-22.16(o)]Maximum Gross Heat Input: Recordkeepingby data acquisition system (DAS) /electronic data storage continuously. Thedata acquisition system (DAS) shall recordgallons per hour. [N.J.A.C. 7:27-22.16(o)]Install equipment: Within 90 days from thedate of the approved permit (BOP080001).The owner or operator shall install andoperate an hourly fuel flow monitor.[N.J.A.C. 7:27-22.16(o)]OS1 Boiler No. 1 firing No. 6 Fuel Oil. Maximum heat input limited to 24.9 MMBtu/hrPage 58 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U40 Two Boilers, each 29.3 MM BTU/hr. firing No. 6 fuel oilOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1NOx (Total) <= 11.6 lb/hr. Maximumemission rate based on maximum gross heatinput to the boiler when firing No. 6 fuel oilfrom operating permit modificationapplication. [N.J.A.C. 7:27-22.16(a)]NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns. See stack test details in OS Summary.[N.J.A.C. 7:27-22.16(o)]NOx (Total): Recordkeeping by stack testresults prior to permit renewal. See stacktest details in OS Summary. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]2SO2 <= 7.82 lb/hr. Maximum emission ratebased on maximum gross heat input to theboiler when firing No. 6 fuel oil fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]None.None.None.3TSP <= 1.04 lb/hr. Maximum emission ratebased on maximum gross heat input to theboiler when firing No. 6 fuel oil fromoperating permit modification application.[N.J.A.C. 7:27-22.16(a)]TSP: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs.See stack test details in OS Summary.[N.J.A.C. 7:27-22.16(o)]TSP: Recordkeeping by stack test resultsprior to permit renewal. See stack testdetails in OS Summary. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack test details in OSSummary. [N.J.A.C. 7:27-22.16(o)]4PM-10 (Total) <= 1.04 lb/hr. Maximumemission rate based on maximum gross heatinput to the boiler when firing No. 6 fuel oilfrom operating permit modificationapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.5Maximum Gross Heat Input <= 24.9MMBTU/hr (HHV). Maximum heat inputrate based on 178 gallons of fuel oil perhour from operating permit minormodification, BOP080001. [N.J.A.C.7:27-22.16(a)]Maximum Gross Heat Input: Monitored byfuel flow/firing rate instrumentcontinuously, based on a 1 hour blockaverage. The owner or operator shall installand operate a fuel flowmeter that shall meetan accuracy of not less than 2% per 40 CFR75, Appendix D. The fuel limit shall be <=178 gallons of fuel oil per hour. [N.J.A.C.7:27-22.16(o)]Maximum Gross Heat Input: Recordkeepingby data acquisition system (DAS) /electronic data storage continuously. Thedata acquisition system (DAS) shall recordgallons per hour. [N.J.A.C. 7:27-22.16(o)]Install equipment: Within 90 days from thedate of the approved permit (BOP080001).The owner or operator shall install andoperate an hourly fuel flow monitor.[N.J.A.C. 7:27-22.16(o)]OS2 Boiler No. 2 firing No. 6 Fuel Oil. Maximum heat input limited to 24.9 MMBtu/hrPage 59 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U100 (6) - Internal Floating Roof Storage Tanks subject to NSPS K, Ka and Kb storing petroleum hydrocarbon and VOC liquidsOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1See GR3 for N.J.A.C. 7:27-16.2 applicablerequirements. [N.J.A.C. 7:27-22.16(a)]Other: See GR3 for N.J.A.C. 7:27-16.2monitoring requirements.[N.J.A.C.7:27-22.16(o)].Other: See GR3 for N.J.A.C. 7:27-16.2recordkeeping requirements.[N.J.A.C.7:27-22.16(a)].Demonstrate compliance: As per theapproved schedule. See GR3 for N.J.A.C.7:27-16.2 submittal or action requirements.[N.J.A.C. 7:27-22.16(a)]2Sulfur Content in Fuel <= 0.2 % sulfur byweight for #2 or lighter, 0.3 % sulfur byweight for #4 and 0.5 % sulfur by weight for#5, #6 & heavier . Maximum allowablesulfur content in fuel oil by fuel oiltype/viscosity and geographic zone for usein New Jersey. [N.J.A.C. 7:27- 9.2(a)]None.None.None.3VOC (Total) <= 110.18 tons in any 12consecutive months. Annual combinedemission limit for all tanks in U100 fromstorage, transfer, roof landing loss,degassing, and cleaning from operatingpermit modification application. [N.J.A.C.7:27-22.16(a)]VOC (Total): Monitored by calculationseach month during operation, based on aconsecutive 12 month period (rolling 1month basis). The owner or operator shallmonitor the type of material (descriptionincluding vapor pressure) stored and theamount of material transferred through thetank each month. In addition, the owner oroperator shall monitor of number of rooflandings each month. Calculations, asspecified in AP-42 (Tanks 4.0 or subsequentversion), shall be performed for eachcalendar month. The results for each monthshall be added to the results for the previous11 months. [N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system each month duringoperation. The owner or operator shallrecord the monitored parameters type andquantity of material transferred and rooflandings) and the emissions per anyconsecutive 12-month period. Theemissions per any consecutive 12-monthperiod shall be calculated by the sum of theemissions calculated during any one monthadded to the sum of the emissions calculatedduring the preceding 11 months. The owneror operator shall start this procedure startingwith the first full month after the approval ofBOP060001. The input and output data ofthe EPA AP42 Tanks program shall bemaintained. [N.J.A.C. 7:27-22.16(o)]None.4HAPs (Total): All HAP emissions are belowreporting threshold from operating permitrenewal application. [N.J.A.C.7:27-22.16(a)]None.None.None.OS SummaryPage 60 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Tank contents limited to petroleumhydrocarbon and VOC liquids with a vaporpressure equal to or less than 11.1 psia, thatare not a HAP as defined at 40 CFR63.1(a)(2). Constituent HAPs in gasolineand fuel oils do not have to be speciated.[N.J.A.C. 7:27-22.16(a)]Other: Tank contents shall be monitored byinvoices, delivery receipts or MSDS foreach different product stored.[N.J.A.C.7:27-22.16(o)].Other: The owner or operator shall maintainreadily accessible records showing vaporpressure and description of each productstored.[N.J.A.C. 7:27-22.16(o)].None.6All requests, reports, applications,submittals, and other communications to theAdministrator pursuant to Part 60 shall besubmitted in duplicate to the RegionalOffice of US Environmental ProtectionAgency. [40 CFR 60.4(a)]None.None.Submit a report: As per the approvedschedule to EPA Region 2 as required by 40CFR 60. [40 CFR 60.4(a)]7All information required to be submitted toEPA under 40 CFR 60.4(a), must also besubmitted to the NJDEP RegionalEnforcement Office. [40 CFR 60.4(b)]None.None.Submit a report: As per the approvedschedule to the appropriate RegionalEnforcement Office of NJDEP as requiredby 40 CFR 60. [40 CFR 60.4(b)]8The owner or operator subject to theprovisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of the date of construction orreconstruction of an affected facility asdefined under 40 CFR Part 60 Subpart A.Notification shall be postmarked no laterthan 30 days after such date. [40 CFR60.7(a)(1)]None.None.Submit notification: Upon occurrence ofevent to EPA Region 2 and the appropriateRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7 [40 CFR60.7(a)(1)]9The owner or operator subject to theprovisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of the actual date of initialstartup of an affected facility postmarkedwithin 15 days after such date. [40 CFR60.7(a)(3)]None.None.Submit notification: Upon occurrence ofevent to EPA Region 2 and the appropriateRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7 [40 CFR60.7(a)(3)]Page 61 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10The owner or operator shall submit anotification of any physical or operationalchange to an existing facility which mayincrease the emission rate of any airpollutant to which a standard applies, unlessthat change is specifically exempted underan applicable subpart or in 40 CFR 60.14(e).This notice shall be postmarked 60 days oras soon as practicable before the change iscommenced and shall include informationdescribing the precise nature of the change,present and proposed emission controlsystems, productive capacity of the facilitybefore and after the change, and theexpected completion date of the change. TheAdministrator may request additionalrelevant information subsequent to thisnotice. [40 CFR 60.7(a)(4)]None.None.Submit notification: Upon occurrence ofevent to EPA Region 2 and the appropriateRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7 [40 CFR60.7(a)(4)]11The owner or operator shall maintainrecords of the occurrence and duration ofany startup, shutdown, or malfunction in theoperation of an affected facility, anymalfunction of air pollution controlequipment or any periods during whichcontinuous monitoring system or monitoringdevice is inoperative. [40 CFR 60.7(b)]None.Other: The owner or operator shall maintainreadily accessible records as required by theapplicable requirement.[40 CFR 60.7(b)].None.12At all times, including periods of start-up,shutdown, and malfunction, owners andoperators shall, to the extent practicable,maintain and operate any affected facilityincluding associated air pollution controlequipment in a manner consistent with goodair pollution control practice for minimizingemissions. Determination of whetheracceptable operating and maintenanceprocedures are being used will be based oninformation available to the Administratorwhich may include, but is not limited to,monitoring results, opacity observations,review of operation and maintenanceprocedures, and inspection of the source.[40 CFR 60.11(d)]None.None.None.Page 62 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement13No owner or operator subject to theprovisions of 40 CFR 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to the atmosphere.[40 CFR 60.12]None.None.None.14Compliance with all applicable standardsmust be achieved within 180 days ofcompletion of any physical or operationalchange subject to the control measuresspecified in 40 CFR Part 60.14(a). [40 CFR60.14(g)]None.None.None.Page 63 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15The owner or operator of an existing facilitythat proposes to replace components, andthe fixed capital cost of the new componentsexceeds 50 percent of the fixed capital costthat would be required to construct acomparable entirely new facility, he shallnotify the Administrator of the proposedreplacements. The notice must bepostmarked 60 days (or as soon aspracticable) before construction of thereplacements is commenced and mustinclude the following information:(1) Name and address of the owner oroperator.(2) The location of the existing facility.(3) A brief description of the existingfacility and the components which are to bereplaced.(4) A description of the existing airpollution control equipment and theproposed air pollution control equipment.(5) An estimate of the fixed capital cost ofthe replacements and of constructing acomparable entirely new facility.(6) The estimated life of the existingfacility after the replacements.(7) A discussion of any economic ortechnical limitations the facility may have incomplying with the applicable standards ofperformance after the proposedreplacements. [40 CFR 60.15(d)]None.None.Submit notification: Upon occurrence ofevent. [40 CFR 60.15(d)]16Changes in time periods for submittal ofinformation and postmark deadlines set forthin this subpart, may be made only uponapproval by the Administrator and shallfollow procedures outlined in 40 CFR Part60.19. [40 CFR 60.19]None.None.None.17The owner or operator shall document andreport to the Administrator within 30 daysafter December 16,1996 the use of theemission screening equations in 40 CFR63.420(a)(1) and the calculated value of ET.[MACT Subpart R] [40 CFR 63.428(j)(1)]None.Other: Maintain a record of the calculationsin 40 CFR 63.420(a)(1) including methods,procedures, and assumptions supporting thecalculation for determining criteria in 40CFR 63.420(d).[40 CFR 63.420(j)(2)].None.Page 64 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement18A facility for which the results, ET, of thecalculation in 40 CFR 63.420(a)(1) has beendocumented and is less than 0.50, is exemptfrom MACT Subpart R, except that theowner or operator shall: Operate the facilitysuch that none of the facility parametersused to calculate the results under 40 CFR63.420(a)(1) is exceeded in any rolling30-day period. [MACT Subpart R] [40 CFR63.420(d)(1)]None.Other: Maintain records and provide reportsin accordance with 40 CFR 63.428(j).[40CFR 63.420(d)(2)].None.19At any time following the notificationrequired under 40 CFR 63.428(j)(1) andprior to any of the parameters beingexceeded, the owner or operator may notifythe Administrator of modifications to thefacility parameters. Each such notifiactionshall document any expected HAP emissionchange resulting from the change inparameter. [MACT Subpart R] [40 CFR63.428(j)(3)]None.None.None.Page 65 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U100 (6) - Internal Floating Roof Storage Tanks subject to NSPS K, Ka and Kb storing petroleum hydrocarbon and VOC liquidsOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Storage vessel shall be equipped with afixed roof in combination with an internalfloating roof.[40 CFR 60.112b(a)(1)]Monitored by visual determination uponinstallation of the control device, prior tofilling, based on an instantaneousdetermination. Visually inspect the internalfloating roof and primary and secondaryseals as specified at 40 CFR 60.113b(a)(1)and (a)(4). [40 CFR 60.113b(a)]Recordkeeping by manual logging ofparameter upon occurrence of event. Theowner or operator shall keep a record ofeach inspection. Each record shall identifythe storage vessel on which the inspectionwas performed and shall contain the date thevessel was inspected and the observedconditions of each component of the controlequipment (seals, internal floating roof, andfittings). The owner or operator shall keep acopy of the records for at least 2 years. [40CFR 60.115b(a)(2)]Submit notification: As per the approvedschedule. The owner operator shall notifythe Administrator in writing at least 30 daysprior to the filling orrefilling of the storagevessel. [40 CFR 60.113b(a)(5)]2The internal floating roof shall rest or floaton the liquid surface (but not necessarily incomplete contact with it) inside a storagevessel that has a fixed roof. The internalfloating roof shall be floating on the liquidat all times except during initial fill andduring those intervals when the storagevessel is completely emptied and refilled.When the roof is resting on the leg supports,the process of filling, emptying, and refillingshall be continuous and shall beaccomplished as rapidly as possible.[40CFR 60.112b(a)(1)(i)]None.None.None.OS1 Tank 32001 - Internal Floating Roof, 13,440,000 gallon capacity storing petroleum hydrocarbon and VOC liquids, OS2 Tank 32002- Internal Floating Roof, 13,119,960 gallon capacity storing petroleum hydrocarbon and VOC liquidsPage 66 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3The internal floating roof shall be equippedwith either (1) a foam- or liquid-filled sealmounted in contact with the liquid(liquid-mounted seal). A liquid-mountedseal means a foam- or liquid- filled sealmounted in contact with the liquid betweenthe wall of the storage vessel and thefloating roof continuously around thecircumference of the tank; (2) two sealsmounted one above the other so thateachforms a continuous closure that completelycovers the space between the wall of thestorage vessel and the edge of the internalfloating roof. The lower seal may be vapormounted but both must be continuous; or (3)a mechanical shoe seal. A mechanical shoeseal is a metal sheet held vertically againstthe wall of the storage vessel by springs orweight levers and is connected by braces tothe floating roof. A flexible coat fabric(envelope) spans the annular space betweenthe metal sheet and the floating roof. [40CFR 60.112b(a)(1)(ii)]Monitored by visual determination annually,based on an instantaneous determination.Visually inspect the vessel as specified at 40CFR 60.113b(a). [40 CFR 60.113b(a)]Recordkeeping by manual logging ofparameter upon occurrence of event. Theowner or operator shall keep a record ofeach inspection. Each record shall identifythe storage vessel on which the inspectionwas performed and shall contain the date thevessel was inspected and the observedconditions of each component of the controlequipment (seals, internal floating roof, andfittings). The owner or operator shall keep acopy of the records for at least 2 years. [40CFR 60.115b(a)(2)]None.4Each opening in a noncontact internalfloating roof except for automatic bleedervents (vacuum breaker vents) and the rimspace vents is to provide a projection belowthe liquid surface.[40 CFR60.112b(a)(1)(iii)]None.None.None.5Each opening in the internal floating roofexcept for leg sleeves, automatic bleedervents, rim space vents, column wells, ladderwells, sample wells, andstub drains is to beequipped with a cover or lid which is to bemaintained in a closed position at all times(i.e., no visible gap) except when the deviceis in actual use. The cover or lid shall beequipped with a gasket. Covers on eachaccess hatch and automatic gauge float wellshall be bolted except when they are inuse.[40 CFR 60.112b(a)(1)(iv)]None.None.None.Page 67 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6Automatic bleeder vents shall be equippedwith a gasket and are to be closed at alltimes when the roof is floating except whenthe roof is being floated off or is beinglanded on the roof leg supports.[40 CFR60.112b(a)(1)(v)]None.None.None.7Rim space vents shall be equipped with agasket and are to be set to open only whenthe internal floating roof is not floating or atthe manufacturers recommended setting.[40CFR 60.112b(a)(1)(vi)]None.None.None.8Each penetration of the internal floating rooffor the purpose of sampling shall be asample well. The sample well shall have aslit fabric cover that covers at least 90% ofthe opening.[40 CFR 60.112b(a)(1)(vii)]None.None.None.9Each penetration of the internal floating roofthat allows for passage of a columnsupporting the fixed roof shall have aflexible fabric sleeve seal or a gasketedsliding cover.[40 CFR 60.112b(a)(1)(viii)]None.None.None.10Each penetration of the internal floating roofthat allows for passage of a ladder shall havea gasketed sliding cover.[40 CFR60.112b(a)(1)(ix)]None.None.None.11If any of the conditions described at 40 CFR60.113b(a)(2) are detected during the annualvisual inspection required by 40 CFR60.113b(a)(2), the owner or operator shallfurnish the Administrator with a reportwhich identifies the storage vessel, thenature of the defects, and the date thestorage vessel was emptied or the nature ofand date the repair was made.[40 CFR60.115b(a)(3)]None.Other: Keep a record of each inspectionperformed as required by 40 CFR60.113b(a)(1), (a)(2), (a)(3) and (a)(4).Each record shall identify the storage vesselon which the inspection was performed andshall contain the date the vessel wasinspected and the observed condition ofeach component of the control equipment(seals, internal floating roof, and fittings).The permittee shall keep a copy of thereport.[40 CFR 60.115b(a)(2)].Submit a report: Upon occurrence of eventto the Administrator within 30 days of theinspection. The report shall identify thestorage vessel and the reason it did not meetthe specifications of 40 CFR 60.113b(a)(3)and list each repair made. [40 CFR60.115b(a)(4)]Page 68 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement12If an inspection required by 40 CFR60.113b(a)(3) that finds holes or tears in theseal or seal fabric, defects in the internalfloating roof, or other control equipmentdefects listed in 40 CFR 60.113b(a)(3)(ii),the owner or operator shall submit a reportidentifying the storage vessel and thereasons it did not meet the specifications of40 CFR 60.112b(a)(1) or 40 CFR60.113b(a)(3) and listeach repair made.[40CFR 60.115b(a)(3)]None.Other: Keep a record of each inspectionperformed as required by 40 CFR60.113b(a)(1), (a)(2), (a)(3) and (a)(4).Each record shall identify the storage vesselon which the inspection was performed andshall contain the date the vessel wasinspected and the observed condition ofeach component of the control equipment(seals, internal floating roof, and fittings).The permittee shall keep a copy of thereport.[40 CFR 60.115b(a)(2)].Submit a report: Upon occurrence of eventto the Administrator within 30 days of theinspection. The report shall identify thestorage vessel and the reason it did not meetthe specifications of 40 CFR 60.113b(a)(3)and list each repair made. [40 CFR60.115b(a)(3)]13The owner or operator shall keep of thedimension of the storage vessel and ananalysis showing the capacity of the storagevessel.[40 CFR 60.116b(b)]None.Recordkeeping by manual logging ofparameter once initially. Records shall bemaintained readily accessible, for the life ofthe source. [40 CFR 60.116b(b)]None.14The owner or operator shall maintain arecord of the VOL stored, the period ofstorage, and the maximum true vaporpressure of that VOL during the respectivestorage period[40 CFR 60.116b(c)]Other: Tank contents.[N.J.A.C.7:27-22.16(o)].Recordkeeping by manual logging ofparameter per change of material. A copy ofthis record shall be kept for at least 2 years.[40 CFR 60.116b(c)]None.15The owner or operator shall notify theAdministrator within 30 days when themaximum true vapor pressure, asdetermined by 40 CFR 60.116b(e), of theliquid in the storage vessel exceeds therespective maximum true vapor pressure foreach volume range described at 40 CFR60.116b(d).[40 CFR 60.116b(d)]None.None.Submit notification: As per the approvedschedule. [40 CFR 60.116b(d)]Page 69 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U100 (6) - Internal Floating Roof Storage Tanks subject to NSPS K, Ka and Kb storing petroleum hydrocarbon and VOC liquidsOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Storage vessel shall be equipped with afloating roof. [40 CFR 60.112(a)(1)]None.None.None.2The owner or operator shall maintain arecord of the petroleum liquid stored, theperiod of storage, and the maximum truevapor pressure of that liquid during therespective storage period. Available data onthe typical Reid vapor pressure and themaximum expected storage temperature ofthe stored product may be used to determinethe maximum true vapor pressure fromnomographs contained in API Bulletin2517, unless the Administrator specificallyrequests that the liquid be sampled, theactual storage temperature determined, andthe Reid vapor pressure determined from thesample(s). The true vapor pressure of eachtype of crude oil with a Reid vapor pressureless than 13.8 kPa (2.0 psia) or whosephysical properties preclude determinationby the recommended method is to bedetermined from available data and recordedif the estimated true vapor pressure isgreater than 6.9 kPa (1.0 psia). [40 CFR60.113(a)], [40 CFR 60.113(b)] and. [40CFR 60.113(c)]None.Recordkeeping by manual logging ofparameter or storing data in a computer datasystem per change of material. The owneror operator shall record the description ofthe stored product, the period of storage andthe maximum true vapor pressure of thestored liquid. [40 CFR 60.113(a)]None.OS3 Tank 21405 - Internal Floating Roof, 8,886,360 gallon capacity storing petroleum hydrocarbon and VOC liquids, OS4 Tank 21406 -Internal Floating Roof, 8,889,846 gallon capacity storing petroleum hydrocarbon and VOC liquids, OS6 Tank 21048 - Internal FloatingRoof, 8,922,522 gallon capacity storing petroleum hydrocarbon and VOC liquidsPage 70 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Emission Unit:U100 (6) - Internal Floating Roof Storage Tanks subject to NSPS K, Ka and Kb storing petroleum hydrocarbon and VOC liquidsOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The owner or operator shall equip eachstorage vessel with a fixed roof with aninternal floating type cover equipped with acontinuous closure device between the tankwall and the cover edge. The cover is to befloating at all times, (i.e., off the legsupports) except during initial fill and whenthe tank is completely emptied andsubsequently refilled. The process ofemptying and refilling when the cover isresting on the leg supports shall becontinuous and shall beaccomplished asrapidly as possible. Each opening in thecover except for automatic bleeder vents andthe rim space vents is to provide a projectionbelow the liquid surface. Each opening inthe cover except for automatic bleeder vents,rim space vents, stub drains and leg sleevesis to be equipped with a cover, seal, or lidwhich is to be maintained in a closedposition at all times (i.e., no visible gap)except when the device is in actual use.Automatic bleeder vents are to be closed atall times when the cover is floating exceptwhen the cover is being floated off or isbeing landed on the leg supports. Rim ventsare to be set to open only when the cover isbeing floated off the leg supports or at themanufacturer's recommended setting. [40CFR 60.112a(a)(2)]None.None.None.OS5 Tank 22107 - Internal Floating Roof, 9,227,526 gallon capacity storing petroleum hydrocarbon and VOC liquidsPage 71 of 72New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 4/13/2010ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement2The owner or operator shall maintain arecord of the petroleum liquid stored, theperiod of storage, and the maximum truevapor pressure of that liquid during therespective storage period. Available data onthe typical Reid vapor pressure and themaximum expected storage temperature ofthe stored product may be used to determinethe maximum true vapor pressure fromnomographs contained in API Bulletin2517, unless the Administrator specificallyrequests that the liquid be sampled, theactual storage temperature determined, andthe Reid vapor pressure determined from thesample(s). The true vapor pressure of eachtype of crude oil with a Reid vapor pressureless than 13.8 kPa (2.0 psia) or whosephysical properties preclude determinationby the recommended method is to bedetermined from available data and recordedif the estimated true vapor pressure isgreater than 6.9 kPa (1.0 psia). [40 CFR60.115a(a)], [40 CFR 60.115a(b)] and [40CFR 60.115a(c)]None.Recordkeeping by manual logging ofparameter or storing data in a computer datasystem per change of material. The owneror operator shall record the description ofthe stored product, the period of storage andthe maximum true vapor pressure of thestored liquid. [40 CFR 60.115a(a)]None.Page 72 of 72

# ST LINDEN TERMINAL LLC S HORESIDE FACILITY (41800) Date: 4/13/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

741,232

403,616

New Jersey State Plane 8

NAD83

DEP-GIS

Other/Unknown

4226 State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC: Union Mailing

Address: Street

Address: 4501 TREMLEY PT RD

LINDEN, NJ 07036

4501 TREMLEY PT RD

LINDEN, NJ 07036 Facility Name (AIMS): ST LINDEN TERMINAL LLC SHORESIDE Facility ID (AIMS): 41800

NAICS:

Page 1 of 5

# ST LINDEN TERMINAL LLC S HORESIDE FACILITY (41800) Date: 4/13/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(908) 862-1906 x

( ) - x NuStar Terminal Operations Partnership L.P.

Timonthy Roessler

Environmentall Manager - East Region

(908) 862-4877 x 3700 South Wood Avenue

Linden, NJ 07036 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 12345678811 Contact Type: BOP - Operating Permits

(732) 830-8401 x

( ) - x

royxx@optonline.net Sullivan Engineering Group, Inc.

LeRoy E. Sullivan, P.E.

Environmental Engineer

(732) 830-8455 x PO Box 637

Normandy Beach, NJ 08739-0637 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Corporation

NJ EIN: 12345678911 Contact Type: Consultant

(908) 862-1906 x

( ) - x NuStar Terminal Operations Partnership L.P.

Timonthy Roessler

Environmentall Manager - East Region

(908) 862-4877 x 3700 South Wood Avenue

Linden, NJ 07036 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 12345678811 Contact Type: Emission Statements

Page 2 of 5

# ST LINDEN TERMINAL LLC S HORESIDE FACILITY (41800) Date: 4/13/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(210) 918-5619 x

( ) - x

stephen.doyle@nustarenergy.com NuStar Energy L.P.

Stephen J. Doyle

Regional HSE Director

(856) 224-8131 x 7 N. Delaware Street

PO Box 149

Paulsboro, NJ 08066 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 12345678811 Contact Type: Environmental Officer

(210) 918-5619 x

( ) - x

stephen.doyle@nustarenergy.com NuStar Energy L.P.

Stephen J. Doyle

Regional HSE Director

(856) 224-8131 x 7 N. Delaware Street

PO Box 149

Paulsboro, NJ 08066 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 12345678811 Contact Type: Fees/Billing Contact

(908) 862-1906 x

( ) - x NuStar Terminal Operations Partnership L.P.

Timonthy Roessler

Environmentall Manager - East Region

(908) 862-4877 x 3700 South Wood Avenue

Linden, NJ 07036 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 12345678811 Contact Type: General Contact

Page 3 of 5

# ST LINDEN TERMINAL LLC S HORESIDE FACILITY (41800) Date: 4/13/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(908) 862-9350 x

( ) - x

dave.jones@nustarenergy.com ST Linden Terminal, LLC

Ian Vaughan

Sr. AreaTerminal Manager

(908) 862-4115 x 4501 Tremley Point Road

Linden, NJ 07036 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 00223613082 Contact Type: On-Site Manager

( ) - x

( ) - x NuStar Terminals Operations Partnership L.P.

NuStar Terminals Operations Partnership

( ) - x Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: NJ EIN: Contact Type: Operator

( ) - x

( ) - x ST Linden Terminal. LLC

ST Linden Terminal. LLC

( ) - x Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: NJ EIN: Contact Type: Owner (Current Primary)

Page 4 of 5

# ST LINDEN TERMINAL LLC S HORESIDE FACILITY (41800) Date: 4/13/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(210) 918-5684 x

( ) - x NuStar Energy L.P.

Michael Truby

General Manager - East Region

(856) 224-8130 x 7 North Delaware Street

PO Box 149

Paulsboror, NJ 08066 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LP

NJ EIN: 00223613082 Contact Type: Responsible Official

Page 5 of 5

# ST LINDEN TERMINAL LLC S HORESIDE FACILITY (41800)

BOP090002



# New Jersey Department of Environmental Protection

Reason for Application Date: 4/13/2010



# Permit Being Modified

Permit Class: BOP Number: 90001

Description

of Modifications: Facility wide storage tanks VOC control plan for all floating roof tanks in accordance with

N.J.A.C. 7:27-16.2(p)1.

Page 1 of 1ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002New Jersey Department of Environmental ProtectionNon-Source Fugitive EmissionsDate:04/13/2010FGNJIDDescription ofActivity CausingEmissionLocationDescriptionReasonable Estimate of Emissions (tpy)VOC(Total)NOxCOSOTSP(Total)PM-10PbHAPS(Total)Other(Total)FG1ValvesThroughout Terminal2.6500.23500000FG2FlangesThroughout Terminal0.1700.02400000FG3Pump SealsThroughout Terminal0.0300.00400000FG4Sample PointsThroughout Terminal3.1900.45600000FG5Open End LinesThroughout Terminal0.0600.00800000FG6Loading Arm ValvesThroughout Terminal1.0000.00000000FG7Land based VesselLoading valves,flanges, pump sealsOn Docks22.8700.00000000Total28.9700.0000.0000.0000.0000.0000.0000.727000000.000Page 1 of 1ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002New Jersey Department of Environmental ProtectionInsignificant Source Emissions4/13/2010Date:ISNJIDSource/GroupDescriptionEquipment TypeLocationDescriptionEstimate of Emissions (tpy)VOC(Total)NOxCOSOTSPPM-10PbHAPS(Total)Other(Total)IS1(4) No. 6 Fuel OilStorage TanksStorage VesselBoiler House andShoreside DikeArea0.110IS2(4) Non-ApplicableVOC Storage TanksStorage VesselShoreside/OfficeDike andWaterfront nearMarine VRU0.009Total0.1190.0000.0000.0000.0000.0000.0000.000000000.000Page 1 of 1Equip.NJIDFacility'sDesignationEquipmentDescriptionEquipment TypeCertificateNumberInstallDateGrandFatheredLast Mod.(Since 1968)Equip.Set IDNew Jersey Department of Environmental ProtectionEquipment InventoryBOP090002ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)4/13/2010Date:E1Tank 32001SBOP0600011/1/1974No1/15/2008IFR Storage Tank in U100 (Kb)Storage VesselE2Tank 32002SBOP0600011/1/1974No1/15/2008Storage Tank IFR U100 (Kb)Storage VesselE5Tank 21405SBOP0600011/1/1975No1/15/2008IFR Storage Tank in U100 (K)Storage VesselE6Tank 21406SBOP0600011/1/1975No1/15/2008IFR Storage Tank in U100 (Kb)Storage VesselE7Tank 22107SBOP0600011/1/1975No1/15/2008IFR Storage Tank in U100 (Ka)Storage VesselE8Tank 21408SBOP0600011/1/1975No1/15/2008IFR Storage Tank in U100 (K)Storage VesselE12Tank 105SBOP040003No11/22/2004Tk. 105 Surge Tank U12 (Kb)Storage VesselE13Boiler 1B02169612/11/1975No12/11/1975Steam Boiler # 1BoilerE14Boiler 2B02169712/11/1975No12/11/1975Steam Boiler # 2BoilerE15Marine VRUM09811610/8/1990No2/1/2004Marine Vessel LoadingEquipmentManufacturing andMaterials HandlingEquipmentPage 1 of 1

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E1 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

13,440,000

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

Yes

Iso boards

1.5

56.00

202.00

Submerged

5,000.00

Internal floating roof tank Cylindrical

Yes No Column-supported Shoe mounted Mechanical Shoe 6.31 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E1 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Used AP-42 to determine emissions Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E2 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

13,119,960

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

No

56.00

202.00

Submerged

4,900.00

Internal floating roof tank Cylindrical

Yes No Column-supported 2 Rim mounted Vapor Mounted Resilient 6.31 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E2 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E5 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

8,886,360

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

No

56.00

170.00

Submerged

4,900.00

Internal floating roof tank Cylindrical

Yes No Column-supported 2 Rim mounted Vapor Mounted Resilient 5.31 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E5 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E6 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

8,889,846

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

No

56.00

170.00

Submerged

4,900.00

Internal floating roof tank Cylindrical

Yes No Column-supported 2 Rim mounted Vapor Mounted Resilient 5.31 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E6 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E7 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

9,227,526

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

No

56.00

170.00

Submerged

4,900.00

Internal floating roof tank Cylindrical

Yes No Column-supported 2 Rim mounted Vapor Mounted Resilient 5.31 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E7 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E8 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

8,922,522

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

No

56.00

170.00

Submerged

4,900.00

Internal floating roof tank Cylindrical

Yes No Column-supported 2 Rim mounted Vapor Mounted Resilient 5.31 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E8 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E12 (Storage Vessel)

**Print Date: 4/13/10**

Is the Shell of the Equipment

Exposed to Sunlight?

Thermal Conductivity of Insulation

[(BTU)(in)(hr)(ft2)(deg F)]: What type of contents is this

storage vessel equipped to

contain by design? Liquids Only

Tank

26,652

gallons

Above Ground

Yes

White

Light Rust

Good

Welded

No

30.00

12.00

Submerged

3,500.00

Internal floating roof tank Cylindrical

Yes No Self-supported 2 None Mechanical Shoe 4.00 Roof gal/min Storage Vessel Type:

Design Capacity:

Units:

Ground Location:

Shell Color:

Description (if other):

Shell Condition:

Paint Condition:

Shell Construction:

Is the Shell Insulated?

Type of Insulation:

Insulation Thickess (in):

Shape of Storage Vessel:

Shell Height (From Ground to Roof

Bottom) (ft):

Length (ft):

Width (ft):

Diameter (ft):

Other Dimension

Description:

Value:

Units:

Fill Method:

Description (if other):

Maximum Design Fill Rate:

Units:

Does the storage vessel have

a roof or an open top?

Roof Type:

Roof Height (From Roof

Bottom

to Roof Top) (ft):

Roof Construction:

Primary Seal Type:

Secondary Seal Type:

Total Number of Seals:

Roof Support:

Does the storage vessel

have a Vapor Return Loop?

Does the storage vessel

have a Conservation Vent?

Have you attached a diagram

showing the location and/or the

configuration of this equipment?

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E12 (Storage Vessel)

**Print Date: 4/13/10**

Comments: Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? No

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E13 (Boiler)

**Print Date: 4/13/10**

Cleaver Brooks

Cleaver Brooks

CB-600-700

29.29

Fire Tube

Non-Utility

Steam Only

1,440.00

Conical burners

Forced

Indirect

Yes

No Manufacturer:

Model:

Maximum Rated Gross

Heat Input (MMBtu/hr -

HHV):

Boiler Type:

Utility Type:

Output Type:

Steam Output (lb/hr):

Fuel Firing Method:

Description (if other):

Draft Type:

Heat Exchange Type: Make:

Type:

Amount (%): Is the boiler using? (check all that apply):

Have you attached a

diagram showing the

location and/or the

configuration of this

equipment?

Have you attached any

manuf.'s data or

specifications to aid the

Dept. in its review of this

application?

Comments: Flue Gas Recirculation

(FGR): Low NOx Burner:

Staged Air Combustion:

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E14 (Boiler)

**Print Date: 4/13/10**

Cleaver Brooks

Cleaver Brooks

CB-600-700

29.29

Fire Tube

Non-Utility

Steam Only

1,440.00

Conical burners

Forced

Indirect

Yes

No Manufacturer:

Model:

Maximum Rated Gross

Heat Input (MMBtu/hr -

HHV):

Boiler Type:

Utility Type:

Output Type:

Steam Output (lb/hr):

Fuel Firing Method:

Description (if other):

Draft Type:

Heat Exchange Type: Make:

Type:

Amount (%): Is the boiler using? (check all that apply):

Have you attached a

diagram showing the

location and/or the

configuration of this

equipment?

Have you attached any

manuf.'s data or

specifications to aid the

Dept. in its review of this

application?

Comments: Flue Gas Recirculation

(FGR): Low NOx Burner:

Staged Air Combustion:

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 E15 (Manufacturing and Materials Handling

**Equipment)**

**Print Date: 4/13/10** Callidus Technologies

Callidus Technologies

not applicable

Hydrocarbon vapor combustor

1.75E+04

other units

barrels/hour loaded

Yes

No Make:

Have you attached any manuf.'s

data or specifications to aid the

Dept. in its review of this

application? Description (if other): Units: Capacity: Type of Manufacturing and Materials

Handling Equipment: Model: Manufacturer:

Comments: Have you attached a diagram

showing the location and/or the

configuration of this equipment?ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)Date:4/13/2010New Jersey Department of Environmental ProtectionControl Device InventoryCDNJIDFacility'sDesignationDescriptionCD TypeInstallDateGrandFatheredLast Mod.(Since 1968)CDSet IDBOP090002CD1Carbon Adsorption Unit1/1/1993No1/1/1993Marine VRUAdsorberPage 1 of 1

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 CD1 (Adsorber)

**Print Date: 4/13/10**

Other

1850

20 100

80 Make:

Manufacturer:

Model:

Maximum Gas Flow Rate to

Adsorber (acfm):

Maximum Temperature of Vapor

Stream to Adsorber (°F):

Minimum Temperature of Vapor

Stream to Adsorber (°F):

Minimum Moisture Content of

Vapor Stream to Adsorber (%): Description: Adsorber Type:

Type of Adsorbant: DualBed IT McGill

IT McGill

1850 ACFM

Activated Carbon

Feet

Regenerated on-site 10.75

Vacuum 10

2 Maximum Pressure Drop Across

Adsorber (in. H20): Other Bed Dimension: Units: Bed Width: Bed Length: Bed Height:

Units: Value:

Minimum Pressure Drop Across

Adsorbant (in. H20):

Total Weight of Adsorbant When

Saturated (lbs): Total Weight of Adsorbant (lbs):

Method of Determining Breakthrough (check all that apply):

Continuous Emissions

Periodic Testing: Replacement By Weight: Monitor (CEM):

Sampling Frequency:

Sampling Device:

Description:

Minimum Concentration at

Breakthrough (ppmvd):

Maximum Number of Sources

Using this Apparatus as a Control

Device (Include Permitted and

Non-Permitted Sources): Handling Method of Saturated

Adsorbant:

Method of Regeneration: Other: Set-up Type: Maximum Adsorbant Capacity (lbs

Adsorbate/lbs Adsorbant):

Minimum Adsorbant Capacity (lbs

Adsorbate/lbs Adsorbant): 40000 5

10 10.5

38600 Diameter

2

Alternative Method to Demonstrate

# 41800 ST LINDEN TERMINAL LLC SHORESIDE FACILITY BOP090002 CD1 (Adsorber)

**Print Date: 4/13/10**

Yes No Yes No Yes No

Comments: Have you attached data from

recent performance testing?

Have you attached any

manufacturer's data or

specifications in support of the

feasibility and/or effectiveness of

this control apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus? Alternative Method to Demonstrate

Control Apparatus is Operating

Properly:ST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)Date:4/13/2010New Jersey Department of Environmental ProtectionEmission Points InventoryPTNJIDFacility'sDesignationDescriptionConfig.Equiv.Diam.(in.)Height(ft.)Dist. toProp.Line (ft)Exhaust Temp. (deg. F)Exhaust Vol. (acfm)Avg.Min.Max.Avg.Min.Max.DischargeDirectionPTSet IDBOP090002PT132001Storage Tank IFRRectangle185510455.040.0125.0HorizontalR1,684.01,124.0562.0PT232002Storage Tank IFRRectangle18569056.451.861.0HorizontalR1,684.01,124.0562.0PT332003Storage Tank Cone RoofRound1856104125.0125.0125.0HorizontalR1,684.01,124.0562.0PT521405Storage Tank IFRRectangle18568456.451.861.0HorizontalR1,684.01,124.0562.0PT621406Storage Tank IFRRectangle18564556.451.861.0HorizontalR1,684.01,124.0562.0PT722107Storage Tank IFRRectangle18568556.451.861.0HorizontalR1,684.01,124.0562.0PT821408Storage Tank IFRRectangle18567856.451.861.0HorizontalR1,684.01,124.0562.0PT9Tank 101Storage Tank HorizontalRound656165125.0125.0125.0HorizontalR1,684.01,124.0562.0PT10Tank 102Storage Tank HorizontalRound656150125.0125.0125.0HorizontalR1,684.01,124.0562.0PT11Tank 104Storage Tank HorizontalRound6564256.451.861.0HorizontalR1,684.01,124.0562.0PT12Tank 105Tank 105 Surge TankRectangle83012059.030.080.0HorizontalR470.050.015.0PT13Boiler 129.3 MMBTU/hr Steam BoilerNo. 1Round2439131390.0390.0390.0UpR8,740.08,740.08,740.0PT14Boiler 229.3 MMBTU/hr Steam BoilerNo. 2Round2439131390.0390.0390.0UpR8,740.08,740.08,740.0PT15M.V.R.U.Marine Vapor RecoveryRound24275056.451.861.0HorizontalR1,872.01,516.0936.0PT16Non-AppMarine Loading ofnon-applicable VOC2501,123.0Page 1 of 1New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Date:4/13/2010U 12 Tank 105 Tank 105 - Internal Floating Roof Surge Tank with a 26,652 gallon capacity storing petroleum hydrocarbon and VOC liquids.UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Tank 105Tank 105 storingpetroleum hydrocarbonand VOC liquids (11.1psia).MaintenanceE12PT12A25-01-995-0002,190.08,760.015.0470.030.080.0U 15 Marine VTO Marine Loading of petroleum hydrocarbon liquids (treated as gasoline) and VOC liquids (applicable and non-applicable)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Gas/VOCLoading of PetroleumHydrocarbon and VOCliquids (vp <= 11.1 psia)with carbon adsorber(CD1)Normal - SteadyStateE15CD1 (P)PT154-03-011-97900.01,800.0140,000.0150,000.0600.01,500.0OS2DistillateLoading of VOC liquids(vp < 0.02 psia) withoutcontrol deviceNormal - SteadyStateE15PT164-03-011-97240.0475.0140,000.0150,000.0600.01,500.0Page 1 of 3New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Date:4/13/2010U 40 Two Boilers Two Boilers, each 29.3 MM BTU/hr. firing No. 6 fuel oilUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Boiler # 1Boiler No. 1 firing No. 6Fuel Oil. Maximum heatinput limited to 24.9MMBtu/hrNormal - SteadyStateE13PT135,300.08,760.08,740.08,740.0390.0390.0OS2Boiler # 2Boiler No. 2 firing No. 6Fuel Oil. Maximum heatinput limited to 24.9MMBtu/hrNormal - SteadyStateE14PT145,300.08,760.08,740.08,740.0390.0390.0U 100 IFR Tanks (6) - Internal Floating Roof Storage Tanks subject to NSPS K, Ka and Kb storing petroleum hydrocarbon andVOC liquidsUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Tank 32001Tank 32001 - InternalFloating Roof, 13,440,000gallon capacity storingpetroleum hydrocarbonand VOC liquidsNormal - SteadyStateE14-04-001-998,760.0OS2Tank 32002Tank 32002 - InternalFloating Roof, 13,119,960gallon capacity storingpetroleum hydrocarbonand VOC liquidsNormal - SteadyStateE24-04-001-998,760.0Page 2 of 3New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryST LINDEN TERMINAL LLC SHORESIDE FACILITY (41800)BOP090002Date:4/13/2010U 100 IFR Tanks (6) - Internal Floating Roof Storage Tanks subject to NSPS K, Ka and Kb storing petroleum hydrocarbon andVOC liquidsUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS3Tank 21405Tank 21405 - InternalFloating Roof, 8,886,360gallon capacity storingpetroleum hydrocarbonand VOC liquidsNormal - SteadyStateE54-04-001-998,760.0OS4Tank 21406Tank 21406 - InternalFloating Roof, 8,889,846gallon capacity storingpetroleum hydrocarbonand VOC liquidsNormal - SteadyStateE64-04-001-998,760.0OS5Tank 22107Tank 22107 - InternalFloating Roof, 9,227,526gallon capacity storingpetroleum hydrocarbonand VOC liquidsNormal - SteadyStateE74-04-001-998,760.0OS6Tank 21408Tank 21048 - InternalFloating Roof, 8,922,522gallon capacity storingpetroleum hydrocarbonand VOC liquidsNormal - SteadyStateE84-04-001-998,760.0Page 3 of 3Date:4/13/2010New Jersey Department of Environmental ProtectionSubject Item Group InventoryGR1 NSPS Kb tkGroup NJID:Members:TypeIDOSStepUU 100OS1 Tank 32001UU 100OS2 Tank 32002UU 100OS6 Tank 21408UU 12OS1 Tank 105Formal Reason(s) for Group/Cap:9OtherOther (explain):Identical compliance plansCondition/Requirements that will be complied with or are no longerapplicable as a result of this Group:Operating Circumstances:Page 1 of 3Date:4/13/2010New Jersey Department of Environmental ProtectionSubject Item Group InventoryGR2 NSPS K, K tkGroup NJID:Members:TypeIDOSStepUU 100OS3 Tank 21405UU 100OS5 Tank 22107UU 100OS6 Tank 21408Formal Reason(s) for Group/Cap:9OtherOther (explain):Identical compliance plansCondition/Requirements that will be complied with or are no longerapplicable as a result of this Group:Operating Circumstances:Page 2 of 3Date:4/13/2010New Jersey Department of Environmental ProtectionSubject Item Group InventoryGR3 Sub 16Group NJID:Members:TypeIDOSStepUU 100OS0 SummaryUU 12OS0 SummaryFormal Reason(s) for Group/Cap:9OtherOther (explain):Common requirementsCondition/Requirements that will be complied with or are no longerapplicable as a result of this Group:Operating Circumstances:Page 3 of 3