### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, March 07, 2011 Page 1 of 21

### Facility Information:

Enter Plant Name (as reported U.S. DOE/EI Enter physical Address

Enter physical city Contact:Person to contact for more detail Phone:Of above person Fax: Of above person Email: Of above person Testing Company: Name of primary testing organization US postal address of above

US postal address of abov Contact:Field test leader Phone:Of above person Fax: Of above person Email:Of above person

Air Permit Number: Enter your facilities ORIS Number here Permitted Source ID/Name: Enter the Boiler ID of the tested boiler (left) SJ10 Permitted Maximum Process Rate: N/A Max. Normal Operation Process Rate: N/A Target Process Test Rate N/A

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: This description should describe the process and associated controls to differentiate this facility from, or document similarity with others of same SCC. Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:Enter ARS ID FRS #:Enter FRS ID

SCC / Description10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Exit 0 0 0 0 0 0 0 0

Target Parameter Test Method Number of

Test RunsTest Run

DurationSample

Points Comments Location% H2O Method 1 - 4 3 180 0 Stack Exit Carbon Monoxide Method 10 3 120 0 Stack Exit Formaldehyde Method 0011 3 120 0 Stack Exit 2,3,7,8-TCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0 Stack Exit



### Monday, March 07, 2011 Page 2 of 211,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 Stack Exit OCDD Method 23 3 480 0 Stack Exit 2,3,7,8-TCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0 Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 Stack Exit OCDF Method 23 3 480 0 Stack Exit Other TCDD Method 23 0 Stack Exit Other PeCDD Method 23 0 Stack Exit Other HxCDD Method 23 0 Stack Exit Other HpCDD Method 23 0 Stack Exit Other TCDF Method 23 0 Stack Exit Other PeCDF Method 23 0 Stack Exit Other HxCDF Method 23 0 Stack Exit Other HpCDF Method 23 0 Stack Exit Total Dioxins Method 23 3 480 0 Stack Exit Total Furans Method 23 3 480 0 Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0 Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 Stack Exit 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 Stack Exit
2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 0 Stack Exit 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 0 Stack Exit 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 Stack Exit

Total PCBs Method 23 3 480 0 Stack Exit Total TEQ Method 23 3 480 0 Stack Exit Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Exit
Hydrogen Chloride Method 26 3 180 0 Stack Exit Hydrogen Fluoride Method 26 3 180 0 Stack Exit Hydrogen Chloride Method 26A 3 180 0 Stack Exit Hydrogen Fluoride Method 26A 3 180 0 Stack Exit Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Organic Condensible

Particulate OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit



### Monday, March 07, 2011 Page 3 of 21

### The following describes any modifications and/or deviations to the applicable test

methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. In this section, identify the promulgation date of any specified test method that you use for determining the procedures followed. This field is also used to document any modifications that are necessary to conduct the emissions test if they are outside the requirements of the cited method. If this modification was approved verbally by a regulatory agency, the name and date of approval should be included. Written formal approval should be attached to this file using the "Attach File" button. Test procedures that are different from those published in the Federal Register should be attached using the "Attach File" button.

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Arsenic Method 29 3 240 0 Stack Exit Nickel Method 29 3 240 0 Stack Exit Selenium Method 29 3 240 0 Stack Exit Lead Method 29 3 240 0 Stack Exit Chromium Method 29 3 240 0 Stack Exit Cadmium Method 29 3 240 0 Stack Exit Manganese Method 29 3 240 0 Stack Exit Beryllium Method 29 3 240 0 Stack Exit Filterable Particulate Method 29 3 240 0 Stack Exit Antimony Method 29 3 240 0 Stack Exit Co2 Method 3A CO2 3 120 0 Stack Exit Co2 Method 3A CO2 3 240 0 Stack Exit O2 Method 3A O2 3 240 0 Stack Exit O2 Method 3A O2 3 480 0 Stack Exit Co2 Method 3A CO2 3 480 0 Stack Exit O2 Method 3A O2 3 120 0 Stack Exit Inorganic (Aqueous)

Condensible Part. Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Organic Condensible

Particulate Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Filterable Particulate Method 5 3 240 0 Stack Exit Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Sulfur Dioxide Method 6C 3 180 0 Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0 Stack Exit



### Monday, March 07, 2011 Page 4 of 21

### Sampling / Stack Data Results Summary



### LocationStack Exit - Method 23 Average Run Number 1 2 3
Test Date 10/18/201010/21/2010 10/22/2010 Run Start Time 8:55:00 AM 8:47:00 AM8:26:00 AM

Run Finish Time 5:04:00 PM4:58:00 PM4:39:00 PM Net Run Time, minutes 380 480 480 Dry Gas Meter Volume Sampled, dscf 168.799 216.228 215.635 200.221 Moisture Content of Stack Gas, % 12.28 9.34 9.80 10.473 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 10.3 10.3 10.2 10.267 Oxygen, % 7.9 8 8.2 8.033 Average Stack Gas Temperature, °F 265.54 267.75 267.10 266.797 Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000 Percent Isokinetic of Sampling Rate, % 95.7 96.6 96.1 96.133 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Monday, March 07, 2011 Page 5 of 21

### LocationStack Exit - Method 29 Average

Run Number
Test Date Run Start Time Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### LocationStack Exit - OTM - 27/28 Average Run Number
Test Date Run Start Time Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf 126 132.5 129.75 129.417 Moisture Content of Stack Gas, % 0.985 0.985 0.985 0.985 Moisture Saturation at Stack Gas Temperature, % 29.84 29.84 29.84 29.840 Carbon Dioxide, % 47.034 47.708 47.034 47.259 Oxygen, % 83.89 84.96 83.89 84.247 Average Stack Gas Temperature, °F 10.1 10.2 10.1 10.133 Dry Volumetric Flow Rate, dry scfm 30.02 30.03 30.02 30.023 Actual Wet Volumetric Flue Gas Flow Rate, acfm 268.52 267.48 268.52 268.173 Percent Isokinetic of Sampling Rate, % 1.070003591 403521.10883896

5096251.070003591

40352 1.083

F-Factor, dscfm/MMBtu @ %O2 0 0 0 0.000
Fw 0 0 0 0.000
Fc 0 0 0 0.000



### Monday, March 07, 2011 Page 6 of 21

### Emissions Summary



### Location: Stack Exit - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000027 0.0000000029 0.0000000028 0.000 lb/mmBtuO2 5.21E-13 4.40E-13 4.33E-13 0.000 ng/dscm 5.65E-04 4.74E-04 4.59E-04 0.000 ng/dscm@7%O2 6.04E-04 5.11E-04 5.02E-04 0.001 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.000000002 0.0000000016 0.000000002 0.000 lb/mmBtuO2 3.86E-13 2.43E-13 3.09E-13 0.000 ng/dscm 4.18E-04 2.61E-04 3.28E-04 0.000 ng/dscm@7%O2 4.47E-04 2.81E-04 3.59E-04 0.000 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.0000000021 0.0000000029 0.000 lb/mmBtuO2 4.25E-13 3.19E-13 4.48E-13 0.000 ng/dscm 4.60E-04 3.43E-04 4.75E-04 0.000 ng/dscm@7%O2 4.92E-04 3.70E-04 5.20E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.0000000019 0.0000000023 0.000 lb/mmBtuO2 4.25E-13 2.88E-13 3.56E-13 0.000 ng/dscm 4.60E-04 3.10E-04 3.77E-04 0.000 ng/dscm@7%O2 4.92E-04 3.34E-04 4.13E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000012 0.0000000012 0.0000000019 0.000 lb/mmBtuO2 2.32E-13 1.82E-13 2.94E-13 0.000 ng/dscm 2.51E-04 1.96E-04 3.11E-04 0.000 ng/dscm@7%O2 2.68E-04 2.11E-04 3.40E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.000000002 0.0000000022 0.000 lb/mmBtuO2 4.25E-13 3.04E-13 3.40E-13 0.000 ng/dscm 4.60E-04 3.27E-04 3.60E-04 0.000 ng/dscm@7%O2 4.92E-04 3.52E-04 3.94E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDF Average



### Monday, March 07, 2011 Page 7 of 21RunNumber 1 2 3 Mass_mg 0.0000000012 0.0000000012 0.0000000016 0.000 lb/mmBtuO2 2.32E-13 1.82E-13 2.47E-13 0.000 ng/dscm 2.51E-04 1.96E-04 2.62E-04 0.000 ng/dscm@7%O2 2.68E-04 2.11E-04 2.87E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000025 0.0000000025 0.0000000024 0.000 lb/mmBtuO2 4.82E-13 3.80E-13 3.71E-13 0.000 ng/dscm 5.23E-04 4.08E-04 3.93E-04 0.000 ng/dscm@7%O2 5.59E-04 4.40E-04 4.30E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000016 0.0000000015 0.0000000021 0.000 lb/mmBtuO2 3.09E-13 2.28E-13 3.25E-13 0.000 ng/dscm 3.35E-04 2.45E-04 3.44E-04 0.000 ng/dscm@7%O2 3.58E-04 2.64E-04 3.77E-04 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000024 0.0000000017 0.0000000021 0.000 lb/mmBtuO2 4.63E-13 2.58E-13 3.25E-13 0.000 ng/dscm 5.02E-04 2.78E-04 3.44E-04 0.000 ng/dscm@7%O2 5.37E-04 3.00E-04 3.77E-04 0.000 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000015 0.0000000014 0.0000000016 0.000 lb/mmBtuO2 2.89E-13 2.13E-13 2.47E-13 0.000 ng/dscm 3.14E-04 2.29E-04 2.62E-04 0.000 ng/dscm@7%O2 3.36E-04 2.47E-04 2.87E-04 0.000 

### Compound:2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000000083 0.0000000145 0.0000000094 0.000 lb/mmBtuO2 1.60E-12 2.20E-12 1.45E-12 0.000 ng/dscm 1.74E-03 2.37E-03 1.54E-03 0.002 ng/dscm@7%O2 1.86E-03 2.55E-03 1.69E-03 0.002 

### Compound:2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.000000164 0.000000147 0.0000000565 0.000 lb/mmBtuO2 3.16E-11 2.23E-11 8.74E-12 0.000 ng/dscm 3.43E-02 2.40E-02 9.25E-03 0.023 ng/dscm@7%O2 3.67E-02 2.59E-02 1.01E-02 0.024



### Monday, March 07, 2011 Page 8 of 21

### Compound:2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.000000384 0.000000366 0.000000147 0.000 lb/mmBtuO2 7.41E-11 5.56E-11 2.27E-11 0.000 ng/dscm 8.03E-02 5.98E-02 2.41E-02 0.055 ng/dscm@7%O2 8.59E-02 6.44E-02 2.64E-02 0.059 

### Compound:2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.000000077 0.0000000708 0.0000000234 0.000 lb/mmBtuO2 1.49E-11 1.07E-11 3.62E-12 0.000 ng/dscm 1.61E-02 1.16E-02 3.83E-03 0.011 ng/dscm@7%O2 1.72E-02 1.25E-02 4.19E-03 0.011 

### Compound:2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.0000000072 0.0000000158 0.0000000111 0.000 lb/mmBtuO2 1.39E-12 2.40E-12 1.72E-12 0.000 ng/dscm 1.51E-03 2.58E-03 1.82E-03 0.002 ng/dscm@7%O2 1.61E-03 2.78E-03 1.99E-03 0.002 

### Compound:2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.00000137 0.00000124 0.00000039 0.000 lb/mmBtuO2 2.64E-10 1.88E-10 6.03E-11 0.000 ng/dscm 2.87E-01 2.03E-01 6.39E-02 0.185 ng/dscm@7%O2 3.07E-01 2.19E-01 6.99E-02 0.199 

### Compound:2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.0000000173 0.0000000158 0.0000000109 0.000 lb/mmBtuO2 3.34E-12 2.40E-12 1.69E-12 0.000 ng/dscm 3.62E-03 2.58E-03 1.79E-03 0.003 ng/dscm@7%O2 3.87E-03 2.78E-03 1.96E-03 0.003 

### Compound:2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000012 0.0000000012 0.0000000016 0.000 lb/mmBtuO2 2.32E-13 1.82E-13 2.47E-13 0.000 ng/dscm 2.51E-04 1.96E-04 2.62E-04 0.000 ng/dscm@7%O2 2.68E-04 2.11E-04 2.87E-04 0.000 

### Compound:2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000023 0.0000000024 0.0000000016 0.000 lb/mmBtuO2 4.44E-13 3.64E-13 2.47E-13 0.000



### Monday, March 07, 2011 Page 9 of 21ng/dscm 4.81E-04 3.92E-04 2.62E-04 0.000 ng/dscm@7%O2 5.14E-04 4.22E-04 2.87E-04 0.000 

### Compound:2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.000000002 0.0000000019 0.000000002 0.000 lb/mmBtuO2 3.86E-13 2.88E-13 3.09E-13 0.000 ng/dscm 4.18E-04 3.10E-04 3.28E-04 0.000 ng/dscm@7%O2 4.47E-04 3.34E-04 3.59E-04 0.000 

### Compound:2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000011 0.0000000011 0.0000000013 0.000 lb/mmBtuO2 2.12E-13 1.67E-13 2.01E-13 0.000 ng/dscm 2.30E-04 1.80E-04 2.13E-04 0.000 ng/dscm@7%O2 2.46E-04 1.94E-04 2.33E-04 0.000 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.0000000065 0.0000000135 0.0000000101 0.000 lb/mmBtuO2 1.25E-12 2.05E-12 1.56E-12 0.000 ng/dscm 1.36E-03 2.21E-03 1.65E-03 0.002 ng/dscm@7%O2 1.45E-03 2.38E-03 1.81E-03 0.002 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.0000000142 0.0000000154 0.0000000084 0.000 lb/mmBtuO2 2.74E-12 2.34E-12 1.30E-12 0.000 ng/dscm 2.97E-03 2.52E-03 1.38E-03 0.002 ng/dscm@7%O2 3.18E-03 2.72E-03 1.51E-03 0.002 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.000000164 0.000000182 0.0000000367 0.000 lb/mmBtuO2 3.16E-11 2.76E-11 5.67E-12 0.000 ng/dscm 3.43E-02 2.97E-02 6.01E-03 0.023 ng/dscm@7%O2 3.67E-02 3.20E-02 6.58E-03 0.025 

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.0000000098 0.00000002 0.0000000112 0.000 lb/mmBtuO2 1.89E-12 3.04E-12 1.73E-12 0.000 ng/dscm 2.05E-03 3.27E-03 1.83E-03 0.002 ng/dscm@7%O2 2.19E-03 3.52E-03 2.00E-03 0.003 

### Compound:OCDD Average RunNumber 1 2 3


### Monday, March 07, 2011 Page 10 of 21Mass_mg 0.000000012 0.0000000054 0.0000000045 0.000 lb/mmBtuO2 2.32E-12 8.20E-13 6.96E-13 0.000 ng/dscm 2.51E-03 8.82E-04 7.37E-04 0.001 ng/dscm@7%O2 2.68E-03 9.50E-04 8.07E-04 0.001 

### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.0000000041 0.000000004 0.0000000053 0.000 lb/mmBtuO2 7.91E-13 6.07E-13 8.20E-13 0.000 ng/dscm 8.58E-04 6.53E-04 8.68E-04 0.001 ng/dscm@7%O2 9.17E-04 7.04E-04 9.50E-04 0.001 

### Compound: Other HpCDD Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound: Other HpCDF Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound:Other HxCDD Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound:Other HxCDF Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound:Other PeCDD Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000



### Monday, March 07, 2011 Page 11 of 21

### Compound: Other PeCDF Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound: Other TCDD Average RunNumber 1 2 3 Mass_mg 0 0.0000000047 0.0000000038 0.000 lb/mmBtuO2 0.00E+00 7.13E-13 5.88E-13 0.000 ng/dscm 0.00E+00 7.68E-04 6.22E-04 0.000 ng/dscm@7%O2 0.00E+00 8.28E-04 6.81E-04 0.001 

### Compound: Other TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000024 0.0000000026 0 0.000 lb/mmBtuO2 4.63E-13 3.95E-13 0.00E+00 0.000 ng/dscm 5.02E-04 4.25E-04 0.00E+00 0.000 ng/dscm@7%O2 5.37E-04 4.58E-04 0.00E+00 0.000 

### Compound:Total Dioxins Average RunNumber 1 2 3 Mass_mg 0.0000000261 0.000000023 0.000000022 0.000 lb/mmBtuO2 5.04E-12 3.49E-12 3.40E-12 0.000 ng/dscm 5.46E-03 3.76E-03 3.60E-03 0.004 ng/dscm@7%O2 5.84E-03 4.05E-03 3.94E-03 0.005 

### Compound:Total Furans Average RunNumber 1 2 3 Mass_mg 0.0000000207 0.0000000203 0.0000000218 0.000 lb/mmBtuO2 3.99E-12 3.08E-12 3.37E-12 0.000 ng/dscm 4.33E-03 3.32E-03 3.57E-03 0.004 ng/dscm@7%O2 4.63E-03 3.58E-03 3.91E-03 0.004 

### Compound:Total PCBs Average RunNumber 1 2 3 Mass_mg 0.0000022223 0.0000021008 0.0000007147 0.000 lb/mmBtuO2 4.29E-10 3.19E-10 1.11E-10 0.000 ng/dscm 4.65E-01 3.43E-01 1.17E-01 0.308 ng/dscm@7%O2 4.97E-01 3.70E-01 1.28E-01 0.332 

### Compound:Total TEQ Average RunNumber 1 2 3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000



### Monday, March 07, 2011 Page 12 of 21ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000



### Location: Stack Exit - Method 29 Compound:Antimony Average RunNumber 1 2 3 Mass_mg 0.5441 0.2751 0.6331 0.484 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 1.37E-04 6.96E-05 1.56E-04 0.000 mg/dscm 1.47E-01 7.49E-02 1.69E-01 0.130 mg/dscm@7%O2 1.60E-01 8.07E-02 1.81E-01 0.141 

### Compound:Arsenic Average RunNumber 1 2 3 Mass_mg 0.0192 0.0092 0.0233 0.017 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 4.85E-06 2.33E-06 5.72E-06 0.000 mg/dscm 5.17E-03 2.51E-03 6.21E-03 0.005 mg/dscm@7%O2 5.61E-03 2.70E-03 6.64E-03 0.005 

### Compound:Beryllium Average RunNumber 1 2 3 Mass_mg 0.0033 0.0013 0.0037 0.003 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 8.33E-07 3.29E-07 9.09E-07 0.000 mg/dscm 8.89E-04 3.54E-04 9.86E-04 0.001 mg/dscm@7%O2 9.65E-04 3.81E-04 1.05E-03 0.001 

### Compound:Cadmium Average RunNumber 1 2 3 Mass_mg 0.0004 0.0004 0.0009 0.001 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 1.01E-07 1.01E-07 2.21E-07 0.000 mg/dscm 1.08E-04 1.09E-04 2.40E-04 0.000 mg/dscm@7%O2 1.17E-04 1.17E-04 2.57E-04 0.000 

### Compound:Chromium Average RunNumber 1 2 3 Mass_mg 0.0322 0.0112 0.0292 0.024 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 8.13E-06 2.84E-06 7.17E-06 0.000 mg/dscm 8.68E-03 3.05E-03 7.78E-03 0.007 mg/dscm@7%O2 9.43E-03 3.29E-03 8.32E-03 0.007 

### Compound:Filterable Particulate Average RunNumber 1 2 3 Mass_mg 0 66.1 154.9 73.667



### Monday, March 07, 2011 Page 13 of 21Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 0.00E+00 1.67E-02 3.81E-02 0.018 mg/dscm 0.00E+00 1.80E+01 4.13E+01 19.767 mg/dscm@7%O2 0.00E+00 1.94E+01 4.42E+01 21.200 

### Compound:Lead Average RunNumber 1 2 3 Mass_mg 0.0406 0.0139 0.0396 0.031 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 1.02E-05 3.52E-06 9.73E-06 0.000 mg/dscm 1.09E-02 3.79E-03 1.05E-02 0.008 mg/dscm@7%O2 1.18E-02 4.08E-03 1.12E-02 0.009 

### Compound:Manganese Average RunNumber 1 2 3 Mass_mg 0.4871 0.2415 0.5351 0.421 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 1.23E-04 6.11E-05 1.31E-04 0.000 mg/dscm 1.31E-01 6.58E-02 1.43E-01 0.113 mg/dscm@7%O2 1.42E-01 7.09E-02 1.53E-01 0.122 

### Compound:Nickel Average RunNumber 1 2 3 Mass_mg 3.2661 1.6336 3.6351 2.845 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 8.24E-04 4.14E-04 8.93E-04 0.001 mg/dscm 8.80E-01 4.45E-01 9.68E-01 0.764 mg/dscm@7%O2 9.56E-01 4.79E-01 1.04E+00 0.825 

### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0063 0.004 0.0066 0.006 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 1.59E-06 1.01E-06 1.62E-06 0.000 mg/dscm 1.70E-03 1.09E-03 1.76E-03 0.002 mg/dscm@7%O2 1.85E-03 1.17E-03 1.88E-03 0.002



### Location: Stack Exit - OTM - 27/28 Compound:Filterable Particulate Average RunNumber 1 2 3 Mass_mg 28.9 27 68.2 41.367 lb/mmBtuO2 2.15E-02 1.98E-02 5.06E-02 0.031 

### Compound:Filterable PM2.5 Average RunNumber 1 2 3 Mass_mg 28.4 25.1 33.4 28.967 lb/mmBtuO2 2.11E-02 1.84E-02 2.48E-02 0.021



### Monday, March 07, 2011 Page 14 of 21

### Process Run Data

Compound:Inorganic (Aqueous) Condensible Pa Average RunNumber 1 2 3 Mass_mg 25.7 10.6 7.4 14.567 lb/mmBtuO2 1.91E-02 7.78E-03 5.50E-03 0.011 

### Compound:Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 2.7 2.6 2.1 2.467 lb/mmBtuO2 2.01E-03 1.91E-03 1.56E-03 0.002 

### Compound:Total Particulate Average RunNumber 1 2 3 Mass_mg 57.3 40.2 77.7 58.400 lb/mmBtuO2 4.26E-02 2.95E-02 5.77E-02 0.043 

### Compound:Total PM2.5 Average RunNumber 1 2 3 Mass_mg 0.5 1.9 34.8 12.400 lb/mmBtuO2 3.71E-04 1.39E-03 2.58E-02 0.009



### Monday, March 07, 2011 Page 15 of 21

### Process Run Data



### Run Name Value UOM Comments Target Value 1 Residual Oil Burned 0 1000 Gallons/million BTU using O2 0


### 1 Average Heat Input 915 MMBtu/hr 0
1 Steam Output 6611000 lb steam/hr 0
1 Synfuel Firing Rate 0 0


### 1 Petroleum Coke Firing Rate 0 0
1 Coal Gas Firing Rate 0 0
1 Fuel Oil Firing Rate 0 0


### 1 Flue Gas Flow Rate 0 dscfm 0
1 Pressure Drop Across FGD (if applicable) 0 in H20 0
1 FGD Scrubber Liquor pH 0 pH 0


### 1 FGD Scrubber Liquor Flow Rate 0 gal/min 0
1 Sorbent Type and Sorbent Injection Rate (if applicable) 0 lb/hr 0



### 1 Flue Gas Oxygen Content 0 % 0
1 Flue Gas Carbon Dioxide Content 0 % 0
1 Flue Gas Moisture Content 0 % 0


### 1 Flue Gas Sampling Point Temperature 0 Deg F 0
1 Flue Gas Pressure 0 atm 0
1 Standard Pressure 0 atm 0


### 1 Standard Temperature 0 Deg F 0
1 Unit Gross Electrical Output 90 MW 0
1 Unit Net Electric Generation 0 MWh 0


### 2Residual Oil Burned 0 1000 Gallons/million BTU using O2 0
2 Average Heat Input 915 MMBtu/hr 0
2 Steam Output 6611000 lb steam/hr 0


### 2 Synfuel Firing Rate 0 0
2Petroleum Coke Firing Rate 0 0
2 Coal Gas Firing Rate 0 0


### 2Fuel Oil Firing Rate 0 0
2Flue Gas Flow Rate 0 dscfm 0
2 Pressure Drop Across FGD (if applicable) 0 in H20 0


### 2FGD Scrubber Liquor pH 0 pH 0
2FGD Scrubber Liquor Flow Rate 0 gal/min 0



### Monday, March 07, 2011 Page 16 of 21

### APCD Run Data

2 Sorbent Type and Sorbent Injection Rate (if applicable) 0 lb/hr 0



### 2Flue Gas Oxygen Content 0 % 0
2Flue Gas Carbon Dioxide Content 0 % 0


### 2Flue Gas Moisture Content 0 % 0
2Flue Gas Sampling Point Temperature 0 Deg F 0
2Flue Gas Pressure 0 atm 0


### 2 Standard Pressure 0 atm 0
2 Standard Temperature 0 Deg F 0
2 Unit Gross Electrical Output 90 MW 0


### 2Unit Net Electric Generation 0 MWh 0
3 Residual Oil Burned 0 1000 Gallons/million BTU using O2 0
3 Average Heat Input 915 MMBtu/hr 0


### 3 Steam Output 6611000 lb steam/hr 0
3 Synfuel Firing Rate 0 0
3 Petroleum Coke Firing Rate 0 0


### 3 Coal Gas Firing Rate 0 0
3 Fuel Oil Firing Rate 0 0
3 Flue Gas Flow Rate 0 dscfm 0


### 3 Pressure Drop Across FGD (if applicable) 0 in H20 0
3 FGD Scrubber Liquor pH 0 pH 0
3 FGD Scrubber Liquor Flow Rate 0 gal/min 0


### 3 Sorbent Type and Sorbent Injection Rate (if applicable) 0 lb/hr 0

3 Flue Gas Oxygen Content 0 % 0


### 3 Flue Gas Carbon Dioxide Content 0 % 0
3 Flue Gas Moisture Content 0 % 0
3 Flue Gas Sampling Point Temperature 0 Deg F 0


### 3 Flue Gas Pressure 0 atm 0
3 Standard Pressure 0 atm 0
3 Standard Temperature 0 Deg F 0


### 3 Unit Gross Electrical Output 90 MW 0
3 Unit Net Electric Generation 0 MWh 0



### Run Name Value UOM Comments Target Value 1 List all emissions control devices in order of 0 0



### Monday, March 07, 2011 Page 17 of 21

### Process Lab Run Data

process flow. Choose from 

### 1 drop down lists. If not on list add description and provide detailed 0 0

1 desription in section 5a. 0 0

Run Name ValueUOM Comments 

### 1 See 4b Comments. 0

Monday, March 07, 2011 Page 18 of 21

### Sampling / Stack Data Results Detail



### LocationStack Exit - Method 23 Average Run Number 1 2 3 Test Date 10/18/201010/21/2010 10/22/2010 Run Start Time 8:55:00 AM8:47:00 AM8:26:00 AM Run Finish Time 5:04:00 PM4:58:00 PM4:39:00 PM Net Traversing Points 19 24 24 Net Run Time, minutes 380 480 480 Nozzle Diameter, inches 0.185 0.185 0.185 0.185 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.985 0.985 0.985 0.985 Barometric Pressure, inches of Mercury 29.85 29.82 29.8 29.823 Average Orifice Meter Differential, inches H2O 0.71 0.68 0.69 0.693 Dry Gas Meter Volume Sampled, cubic feet 177.441 227.447 227.634 210.841 Average Dry Gas Meter Temperature, °F 86.38 86.15 87.75 86.760 Dry Gas Meter Volume Sampled, dscf 168.799 216.228 215.635 200.221 Total Moisture Liquid collected, g 502.1 473.1 497.9 491.033 Volume of Water Vapor, standard cubic feet 23.63 22.27 23.44 23.113 Moisture Content of Stack Gas, % 12.28 9.34 9.80 10.473 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8772 0.9066 0.902 0.895 Carbon Dioxide, % 10.3 10.3 10.2 10.267 Oxygen, % 7.9 8 8.2 8.033 Carbon Monoxide & Nitrogen, % 81.8 81.7 81.6 81.700 Fuel Factor 1.26 1.25 1.25 Dry Molecular Weight, lb/lb-Mole 29.96 29.97 29.96 29.963 Wet Molecular weight, lb/lb-Mole 28.49 28.85 28.79 28.710 Flue Gas Static Pressure, inches of H2O 1 1.5 1.5 1.333 Absolute Flue Gas Pressure, inches of Mercury 29.92 29.93 29.91 29.920 Average Stack Gas Temperature, °F 265.54 267.75 267.10 266.797 Average Velocity Head, inches of H2O 0.9603937708 482430.921953496

4926720.932537301

645413 0.938
Average Stack Gas Velocity, feet/second 64.93 63.30 63.72 63.983 Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000 Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000 Percent Isokinetic of Sampling Rate, % 95.7 96.6 96.1 96.133 Percent Excess Air, % 57.7 59.0 61.5 59.400 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 0 0 0 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Monday, March 07, 2011 Page 19 of 21

### LocationStack Exit - Method 29 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Monday, March 07, 2011 Page 20 of 21

### LocationStack Exit - OTM - 27/28 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Stack Exit Stack Exit Stack Exit Pitot Tube Coefficient 10/19/201010/20/2010 10/20/2010 Dry Gas Meter Calibration Factor OTM - 27/28OTM - 27/28OTM - 27/28 Barometric Pressure, inches of Mercury 1 2 3 2.000 Average Orifice Meter Differential, inches H2O 1:16:00 PM5:02:00 PM 1:16:00 PM Dry Gas Meter Volume Sampled, cubic feet 3:25:45 PM7:14:30 PM3:25:45 PM Average Dry Gas Meter Temperature, °F 24 24 24 24.000 Dry Gas Meter Volume Sampled, dscf 126 132.5 129.75 129.417 Total Moisture Liquid collected, g 0.153 0.153 0.153 0.153 Volume of Water Vapor, standard cubic feet 0.84 0.84 0.84 0.840 Moisture Content of Stack Gas, % 0.985 0.985 0.985 0.985 Moisture Saturation at Stack Gas Temperature, % 29.84 29.84 29.84 29.840 Dry Mole Fraction 0.40 0.40 0.40 0.400 Carbon Dioxide, % 47.034 47.708 47.034 47.259 Oxygen, % 83.89 84.96 83.89 84.247 Carbon Monoxide & Nitrogen, % 44.899 45.453 44.899 45.084 Fuel Factor 108 102.8 108 Dry Molecular Weight, lb/lb-Mole 5.08 4.84 5.08 5.000 Wet Molecular weight, lb/lb-Mole 10.16 9.62 10.16 9.980 Flue Gas Static Pressure, inches of H2O 100.00 100.00 100.00 100.000 Absolute Flue Gas Pressure, inches of Mercury 0.8984 0.9038 0.8984 0.900 Average Stack Gas Temperature, °F 10.1 10.2 10.1 10.133 Average Velocity Head, inches of H2O 8.2 8.2 8.2 8.200 Average Stack Gas Velocity, feet/second 81.7 81.6 81.7 81.667 Stack Cross-Sectional Area, square feet 2.5 2.6 2.5 2.533 Dry Volumetric Flow Rate, dry scfm 30.02 30.03 30.02 30.023 Actual Wet Volumetric Flue Gas Flow Rate, acfm 268.52 267.48 268.52 268.173 Percent Isokinetic of Sampling Rate, % 1.0700035914 03521.108838965

096251.070003591

40352 1.083

Percent Excess Air, % 68.27 69.34 68.27 68.627 F-Factor, dscfm/MMBtu @ %O2 0 0 0 0.000 Round Duct Diameter, inches 1.26 1.25 1.26 Rectangular Duct Width, inches 29.94 29.96 29.94 Rectangular Duct Length, inches 28.73 28.81 28.73 Fw 0 0 0 0.000 Fc 0 0 0 0.000



### Monday, March 07, 2011 Page 21 of 21