### APPENDIX 5A. ENGINEERING RESULTS USED IN THE SHIPMENTS,

NATIONAL IMPACTS, AND LIFE­CYCLE COST SUBGROUP ANALYSES

TABLE O F CONTENTS

**5A.1 I**  **NTRODUCTION**

**.................................. ................................................................**  **5A­1**

**5A.2 G**  **ENERAL S**  **ERVICE FLUORESCENT**  **LAMPS................................................. 5A­1** 

**5A.2.1 S**  **ystems U**  **sed in**  **the Shipments**  **Analysis and**  **NIA**

**.................................... 5A­1** 

**5A.2.1.1 4**  **­foot M**  **edium Bipin**  **General Service**  **Fluorescent Lamps** 

**............ 5A­2** 

**5A.2.1.2 8**  **­foot S**  **ingle Pin**  **Slimline General**  **Service Fluorescent**  **Lamps**

**.... 5A­6** 

**5A.2.1.3 8**  **­foot R**  **ecessed Double**  **Contact High**  **Output General**  **Service**

**Fluorescent L**  **amps**

**.......................................................................... 5A­8** 

**5A.2.1.4 4**  **­foot T5**  **Miniature Bipin**  **Standard Output**  **General Service** 

**Fluorescent L**  **amps**

**........................................................................ 5A­10** 

**5A.2.1.5 4**  **­foot T5**  **Miniature Bipin**  **High Output**  **General Service** 

**Fluorescent L**  **amps**

**........................................................................ 5A­11** 

**5A.2.2 S**  **ystems U**  **sed by**  **Consumers of**  **T12 Electronic**  **Ballasts**

**......................... 5A­12** 

**5A.2.2.1 4**  **­foot M**  **edium Bipin**  **General Service**  **Fluorescent Lamps** 

**.......... 5A­12** 

**5A.2.2.2 8**  **­foot S**  **ingle Pin**  **Slimline General**  **Service Fluorescent**  **Lamps**

**.. 5A­14** 

**5A.2.2.3 8**  **­foot R**  **ecessed Double**  **Contact High**  **Output General**  **Service**

**Fluorescent L**  **amps**

**........................................................................ 5A­15** 

**5A.3 I**  **NCANDESCENT REFLECTOR**  **L AMPS..........................................................**  **5A­16**

LIST O F TABLES

**Table 5**  **A.2.1 4­foot**  **T8 Medium**  **Bipin 3­Lamps**  **per Ballast**  **Lamp­and­Ballast Designs**  **in**

**the C**  **ommercial Sector................................................................................**  **5A­2**

**Table 5A.2.2**  **4­foot T12**  **Medium Bipin**  **Lamp­and­Ballast Designs**  **in the**  **Commercial**

**Sector**

**.......................................................................................................... 5A­3** 

**Table 5A.2.3**  **4­foot T8**  **Medium Bipin**  **2­Lamps per**  **Ballast Lamp­and­Ballast**  **Designs in** 

**the C**  **ommercial and**  **Residential Sector......................................................**  **5A­3**

**Table 5A.2.4**  **4­foot T12**  **Medium Bipin**  **2­Lamps per**  **Ballast Lamp­and­Ballast**  **Designs**

**in t**  **he Residential**  **Sector**

**............................................................................. 5A­5** 

**Table 5A.2.5**  **8­foot T8**  **Single Pin**  **Slimline 2­Lamps**  **per Ballast**  **Lamp­and­Ballast**

**Designs i**  **n the**  **Commercial Sector..............................................................**  **5A­6**

**Table 5A.2.6**  **8­foot T12**  **Single Pin**  **Slimline 2­Lamps**  **per Ballast**  **Lamp­and­Ballast**

**Designs i**  **n the**  **Commercial Sector..............................................................**  **5A­7**

**Table 5A.2.7**  **8­foot T8**  **Recessed Double**  **Contact High**  **Output 2­Lamps**  **per Ballast** 

**Lamp­and­Ballast D**  **esigns in**  **the Industrial**  **Sector**

**.................................... 5A­8** 

**Table 5A.2.8**  **8­foot T12**  **Recessed Double**  **Contact High**  **Output 2­Lamps**  **per Ballast** 

**Lamp­and­Ballast D**  **esigns in**  **the Industrial**  **Sector**

**.................................... 5A­9** 

**Table 5A.2.9**  **4­foot T5**  **Miniature Bipin**  **Standard Output**  **2­Lamps per**  **Ballast Lamp** 

**and­Ballast D**  **esigns in**  **the Commercial**  **Sector**

**........................................ 5A­10** 

**Table 5A.2.10**  **4­foot T5**  **Miniature Bipin**  **High Output**  **2­Lamps per**  **Ballast Lamp­and** 

**Ballast D**  **esigns in**  **the Industrial**  **Sector.................................................... 5A­11** 

**5A­i**

### Table **5A.2.11 4­foot**  **T8 Medium**  **Bipin 3­Lamps**  **per Ballast**  **Lamp­and­Ballast Designs** 

**in t**  **he Commercial**  **and Industrial**  **Sectors................................................. 5A­12** 

**Table 5A.2.12**  **4­foot T12**  **Medium Bipin**  **3­Lamps per**  **Ballast Lamp­and­Ballast**  **Designs**

**in t**  **he Commercial**  **and Industrial**  **Sectors................................................. 5A­12** 

**Table 5A.2.13**  **4­foot T8**  **Medium Bipin**  **2­Lamps per**  **Ballast Lamp­and­Ballast**  **Designs**

**in t**  **he Residential**  **Sector**

**........................................................................... 5A­13** 

**Table 5A.2.14**  **4­foot T12**  **Medium Bipin**  **2­Lamps per**  **Ballast Lamp­and­Ballast**  **Designs**

**in t**  **he Residential**  **Sector**

**........................................................................... 5A­13** 

**Table 5A.2.15**  **8­foot T8**  **Single Pin**  **Slimline 2­Lamps**  **per Ballast**  **Lamp­and­Ballast**

**Designs i**  **n the**  **Commercial and**  **Industrial Sectors** 

**................................... 5A­14** 

**Table 5A.2.16**  **8­foot T12**  **Single Pin**  **Slimline 2­Lamps**  **per Ballast**  **Lamp­and­Ballast**

**Designs i**  **n the**  **Commercial and**  **Industrial Sectors** 

**................................... 5A­14** 

**Table 5A.2.17**  **8­foot T8**  **Recessed Double**  **Contact High**  **Output 2­Lamps**  **per Ballast** 

**Lamp­and­Ballast D**  **esigns in**  **the Industrial**  **Sector**

**.................................. 5A­15** 

**Table 5A.2.18**  **8­foot T12**  **Recessed Double**  **Contact High**  **Output 2­Lamps**  **per Ballast** 

**Lamp­and­Ballast D**  **esigns in**  **the Industrial**  **Sector**

**.................................. 5A­15** 

**Table 5A.3.1**  **90W PAR38**  **Incandescent Reflector**  **Lamps**

**................................................... 5A­16** 

**Table 5A.3.2**  **75W PAR38**  **Incandescent Reflector**  **Lamps**

**................................................... 5A­17** 

**Table 5A.3.3**  **50W PAR30**  **Incandescent Reflector**  **Lamps**

**................................................... 5A­18** 

**5A­ii**

### APPENDIX 5A. ENGINEERING RESULTS USED IN THE SHIPMENTS, NATIONAL

IMPACTS, A ND LIFE­CYCLE COST SUBGROUP ANALYSES

5A.1 I NTRODUCTION

**This a**  **ppendix presents**  **the engineering**  **results used**  **in the**  **shipments analysis,**  **national**

**impacts analysis**  **(NIA), and**  **life­cycle cost**  **(LCC) subgroup**  **analysis. In**  **addition to**  **many of**  **the**

**lamp and**  **lamp­and­ballast designs**  **considered in**  **the primary**  **LCC and**  **payback period**  **(PBP)**

**analysis, the**  **shipments analysis**  **and national**  **impact analysis**  **(NIA) includes**  **designs that**  **do not** 

**save energy**  **or do**  **not emit**  **lumens within**  **10 percent**  **of the**  **baseline lamp­and­ballast**  **system.**

**Product substitutions**  **like reflector**  **compact fluorescent**  **lamps (CFL)**  **that are**  **not included**  **in the** 

**LCC and**  **PBP analysis**  **are also**  **considered in**  **the NIA**  **and shipments**  **analysis. Furthermore,**  **the**

**LCC subgroup**  **analysis contains**  **an assessment**  **of LCC**  **and PBP**  **results for**  **consumers of** 

**fluorescent T12**  **electronic baseline**  **lamp­and­ballast systems,**  **and the**  **engineering results**  **for**

**those systems**  **are presented**  **in this**  **appendix.**

5A.2 G ENERAL SERVICE FLUORESCENT LAMPS

5A.2.1 S ystems Used in the Shipments Analysis and NIA

**The f**  **ollowing tables**  **list the**  **lamp­and­ballast designs**  **used in**  **the general**  **service**

**fluorescent lamp**  **(GSFL) shipments**  **analysis and**  **the NIA.**  **In addition**  **to many**  **of the**  **lamp­and**

**ballast designs**  **considered in**  **the LCC**  **and PBP**  **analysis, the**  **shipments analysis**  **and NIA**  **include**

**designs that**  **do not**  **save energy**  **or do**  **not emit**  **lumens within**  **10 percent**  **of the**  **baseline lamp** 

**and­ballast system.** 

**5A­1**

### 5A.2.1.1 4­foot Medium Bipin General Service Fluorescent Lamps

Table 5 A.2.1 4­foot T8 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**2 32.5**  **8 6.2**  **2 ,802**  **2 ,520**  **2 0,000**  **E lectronic**  **0 .88**  **8 6.8**  **7 ,396**  **6 ,653** 

**3 32.5**  **9 0.8**  **2 ,951**  **2 ,710**  **2 0,000**  **E lectronic**  **0 .88**  **8 6.8**  **7 ,791**  **7 ,154** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .88**  **8 6.8**  **7 ,919**  **7 ,524** 

**5 32.5**  **9 5.4**  **3 ,101**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .88**  **8 6.8**  **8 ,185**  **7 ,696** 

**4 30.4**  **9 3.8**  **2 ,852**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .88**  **8 0.4**  **7 ,528**  **7 ,075** 

**5 28.4**  **9 6.0**  **2 ,726**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .88**  **6 9.7**  **7 ,198**  **6 ,758** 

**4 26.6**  **9 3.0**  **2 ,474**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .88**  **6 6.5**  **6 ,531**  **6 ,204** 

**2 32.5**  **8 6.2**  **2 ,802**  **2 ,520**  **2 0,000**  **E lectronic**  **0 .78**  **7 7.9**  **6 ,556**  **5 ,897** 

**3 32.5**  **9 0.8**  **2 ,951**  **2 ,710**  **2 0,000**  **E lectronic**  **0 .78**  **7 7.9**  **6 ,905**  **6 ,341** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .78**  **7 7.9**  **7 ,019**  **6 ,669** 

**5 32.5**  **9 5.4**  **3,101 2,915**  **2 4,000**  **E lectronic**  **0 .78**  **7 7.9**  **7 ,255**  **6 ,821** 

**4 30.4**  **9 3.8**  **2 ,852**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .78**  **7 2.2**  **6 ,673**  **6 ,271** 

**5 28.4**  **9 6.0**  **2 ,726**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .78**  **6 7.0**  **6 ,380**  **5 ,990** 

**4 26.6**  **9 3.0**  **2 ,474**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .78**  **5 9.4**  **5 ,789**  **5 ,499** 

**2 32.5**  **8 6.2**  **2 ,802**  **2 ,520**  **2 0,000**  **E lectronic**  **0 .71**  **7 1.7**  **5 ,967**  **5 ,368** 

**3 32.5**  **9 0.8**  **2 ,951**  **2 ,710**  **2 0,000**  **E lectronic**  **0 .71**  **7 1.7**  **6 ,286**  **5 ,772** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .71**  **7 1.7**  **6 ,389**  **6 ,071** 

**5 32.5**  **9 5.4**  **3 ,101**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .71**  **7 1.7**  **6 ,604**  **6 ,209** 

**4 30.4**  **9 3.8**  **2 ,852**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .71**  **6 6.4**  **6 ,074**  **5 ,708** 

**5 28.4**  **9 6.0**  **2 ,726**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .71**  **6 1.6**  **5 ,807**  **5 ,453** 

**4 26.6**  **9 3.0**  **2 ,474**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .71**  **5 4.5**  **5 ,269**  **5 ,006** 

***** **Al l**  **s ystems**  **use 3**  **lamps per**  **ballast.**

**5A­2**

### Table 5A.2.2 4­foot T12 Medium Bipin Lamp­and­Ballast Designs in the Commercial

SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 41.0**  **7 8.0**  **3 ,198**  **2 ,880**  **2 0,000**  **M agnetic**  **0 .95**  **1 29.0**  **9 ,114**  **8 ,208** 

**1 41.0**  **8 0.5**  **3 ,301**  **3 ,000**  **2 0,000**  **M agnetic**  **0 .95**  **1 29.0**  **9 ,406**  **8 ,550** 

**1 41.0**  **8 2.9**  **3 ,399**  **3 ,060**  **2 4,000**  **M agnetic**  **0 .95**  **1 29.0**  **9 ,687**  **8 ,721** 

**2 41.0**  **8 7.8**  **3 ,600**  **3 ,250**  **2 4,000**  **M agnetic**  **0 .95**  **1 29.0**  **1 0,259**  **9 ,263** 

**0 34.0**  **7 7.9**  **2 ,649**  **2 ,300**  **2 0,000**  **M agnetic**  **0 .88**  **1 08.0**  **6 ,992**  **6 ,072** 

**1 34.0**  **8 2.4**  **2 ,802**  **2 ,460**  **2 0,000**  **M agnetic**  **0 .88**  **1 08.0**  **7 ,396**  **6 ,494** 

**2 34.0**  **8 5.3**  **2 ,900**  **2 ,610**  **2 0,000**  **M agnetic**  **0 .88**  **1 08.0**  **7 ,657**  **6 ,890** 

**3 34.0**  **9 1.2**  **3 ,101**  **2 ,790**  **2 4,000**  **M agnetic**  **0 .88**  **1 08.0**  **8 ,186**  **7 ,366** 

**0 41.0**  **7 8.0**  **3 ,198**  **2 ,880**  **2 0,000**  **E lectronic**  **0 .88**  **1 07.7**  **8 ,443**  **7 ,603** 

**1 41.0**  **8 0.5**  **3 ,301**  **3 ,000**  **2 0,000**  **E lectronic**  **0 .88**  **1 07.7**  **8 ,713**  **7 ,920** 

**1 41.0**  **8 2.9**  **3 ,399**  **3,060 24,000**  **E lectronic**  **0 .88**  **1 07.7**  **8 ,973**  **8 ,078** 

**2 41.0**  **8 7.8**  **3 ,600**  **3 ,250**  **2 4,000**  **E lectronic**  **0 .88**  **1 07.7**  **9 ,503**  **8 ,580** 

**0 34.0**  **7 7.9**  **2 ,649**  **2 ,300**  **2 0,000**  **E lectronic**  **0 .88**  **9 1.7**  **6 ,992**  **6 ,072** 

**1 34.0**  **8 2.4**  **2 ,802**  **2 ,460**  **2 0,000**  **E lectronic**  **0 .88**  **9 1.7**  **7 ,396**  **6 ,494** 

**2 34.0**  **8 5.3**  **2 ,900**  **2 ,610**  **2 0,000**  **E lectronic**  **0 .88**  **9 1.7**  **7 ,657**  **6 ,890** 

**3 34.0**  **9 1.2**  **3 ,101**  **2 ,790**  **2 4,000**  **E lectronic**  **0 .88**  **9 1.7**  **8 ,186**  **7 ,366** 

**0 41.0**  **7 8.0**  **3 ,198**  **2 ,880**  **2 0,000**  **E lectronic**  **0 .86**  **1 06.3**  **8 ,251**  **7 ,430** 

**1 41.0**  **8 0.5**  **3 ,301**  **3 ,000**  **2 0,000**  **E lectronic**  **0 .86**  **1 06.3**  **8 ,515**  **7 ,740** 

**1 41.0**  **8 2.9**  **3 ,399**  **3 ,060**  **2 4,000**  **E lectronic**  **0 .86**  **1 06.3**  **8 ,769**  **7 ,895** 

**2 41.0**  **8 7.8**  **3 ,600**  **3 ,250**  **2 4,000**  **E lectronic**  **0 .86**  **1 06.3**  **9 ,287**  **8 ,385** 

**0 34.0**  **7 7.9**  **2 ,649**  **2 ,300**  **2 0,000**  **E lectronic**  **0 .86**  **9 0.3**  **6 ,833**  **5 ,934** 

**1 34.0**  **8 2.4**  **2 ,802**  **2 ,460**  **2 0,000**  **E lectronic**  **0 .86**  **9 0.3**  **7 ,228**  **6 ,347** 

**2 34.0**  **8 5.3**  **2 ,900**  **2 ,610**  **2 0,000**  **Electronic 0.86**  **9 0.3**  **7 ,483**  **6 ,734** 

**3 34.0**  **9 1.2**  **3 ,101**  **2 ,790**  **2 4,000**  **E lectronic**  **0 .86**  **9 0.3**  **8 ,000**  **7 ,198** 

***** **Al l**  **e lectronic**  **systems use**  **3 lamps**  **per ballast.**  **All magnetic**  **systems use**  **a 2­lamp**  **ballast and**  **a 1­lamp**  **ballast.**



### Table 5A.2.3 4­foot T8 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Residential Sector

**5A­3**EfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**2 32.5**  **8 6.2**  **2 ,802**  **2 ,520**  **2 0,000**  **E lectronic**  **0 .88**  **5 8.6**  **4 ,931**  **4 ,435** 

**3 32.5**  **9 0.8**  **2 ,951**  **2 ,710**  **2 0,000**  **E lectronic**  **0 .88**  **5 8.6**  **5 ,194**  **4 ,770** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .88**  **5 8.6**  **5 ,280**  **5 ,016** 

**5 32.5**  **9 5.4**  **3 ,101**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .88**  **5 8.6**  **5 ,457**  **5 ,130** 

**4 30.4**  **9 3.8**  **2 ,852**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .88**  **5 4.6**  **5 ,019**  **4 ,717** 

**5 28.4**  **9 6.0**  **2 ,726**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .88**  **5 1.2**  **4 ,798**  **4 ,506** 

**4 26.6**  **9 3.0**  **2 ,474**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .88**  **4 5.4**  **4 ,354**  **4 ,136** 

**2 32.5**  **8 6.2**  **2 ,802**  **2 ,520**  **2 0,000**  **E lectronic**  **0 .78**  **5 1.6**  **4 ,370**  **3 ,931** 

**3 32.5**  **9 0.8**  **2 ,951**  **2 ,710**  **2 0,000**  **E lectronic**  **0 .78**  **5 1.6**  **4 ,604**  **4 ,228** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .78**  **5 1.6**  **4 ,680**  **4 ,446** 

**5 32.5**  **9 5.4**  **3 ,101**  **2 ,915**  **24,000 Electronic**  **0 .78**  **5 1.6**  **4 ,837**  **4 ,547** 

**4 30.4**  **9 3.8**  **2 ,852**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .78**  **4 8.9**  **4 ,448**  **4 ,181** 

**5 28.4**  **9 6.0**  **2 ,726**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .78**  **4 5.6**  **4 ,253**  **3 ,994** 

**4 26.6**  **9 3.0**  **2 ,474**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .78**  **4 0.5**  **3 ,859**  **3 ,666** 

**2 32.5**  **8 6.2**  **2 ,802**  **2 ,520**  **2 0,000**  **E lectronic**  **0 .71**  **4 6.8**  **3 ,978**  **3 ,578** 

**3 32.5**  **9 0.8**  **2 ,951**  **2 ,710**  **2 0,000**  **E lectronic**  **0 .71**  **4 6.8**  **4 ,190**  **3 ,848** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .71**  **4 6.8**  **4 ,260**  **4 ,047** 

**5 32.5**  **9 5.4**  **3 ,101**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .71**  **4 6.8**  **4 ,403**  **4 ,139** 

**4 30.4**  **9 3.8**  **2 ,852**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .71**  **4 4.9**  **4 ,049**  **3 ,806** 

**5 28.4**  **9 6.0**  **2 ,726**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .71**  **4 1.7**  **3 ,871**  **3 ,635** 

**4 26.6**  **9 3.0**  **2 ,474**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .71**  **3 7.0**  **3 ,513**  **3 ,337** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­4**

### Table 5A.2.4 4­foot T12 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Residential SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**1 34.0**  **8 2.4**  **2 ,802**  **2 ,460**  **2 0,000**  **E lectronic**  **0 .75**  **4 8.0**  **4 ,202**  **3 ,690** 

**2 34.0**  **8 5.3**  **2 ,900**  **2 ,610**  **2 0,000**  **E lectronic**  **0 .75**  **4 8.0**  **4 ,350**  **3 ,915** 

**3 34.0**  **9 1.2**  **3 ,101**  **2 ,790**  **2 4,000**  **E lectronic**  **0 .75**  **4 8.0**  **4 ,651**  **4 ,185** 

**0 41.0**  **7 6.8**  **3 ,149**  **2 ,860**  **1 5,000**  **M agnetic**  **0 .68**  **7 0.0**  **4 ,282**  **3 ,890** 

**0 41.0**  **8 0.5**  **3 ,301**  **3 ,000**  **2 0,000**  **M agnetic**  **0 .68**  **7 0.0**  **4 ,489**  **4 ,080** 

**1 41.0**  **8 2.9**  **3 ,399**  **3 ,060**  **2 4,000**  **M agnetic**  **0 .68**  **7 0.0**  **4 ,623**  **4 ,162** 

**2 41.0**  **8 7.8**  **3 ,600**  **3 ,250**  **2 4,000**  **M agnetic**  **0 .68**  **7 0.0**  **4 ,896**  **4 ,420** 

**1 34.0**  **8 2.4**  **2 ,802**  **2 ,460**  **2 0,000**  **M agnetic**  **0 .66**  **6 0.0**  **3 ,698**  **3 ,247** 

**2 34.0**  **8 5.3**  **2 ,900**  **2 ,610**  **2 0,000**  **M agnetic**  **0 .66**  **6 0.0**  **3 ,828**  **3 ,445** 

**3 34.0**  **9 1.2**  **3 ,101**  **2 ,790**  **2 4,000**  **M agnetic**  **0 .66**  **6 0.0**  **4 ,093**  **3 ,683** 

**0 41.0**  **7 6.8**  **3 ,149**  **2,860 15,000**  **E lectronic**  **0 .65**  **5 8.0**  **4 ,093**  **3 ,718** 

**0 41.0**  **8 0.5**  **3 ,301**  **3 ,000**  **2 0,000**  **E lectronic**  **0 .65**  **5 8.0**  **4 ,291**  **3 ,900** 

**1 41.0**  **8 2.9**  **3 ,399**  **3 ,060**  **2 4,000**  **E lectronic**  **0 .65**  **5 8.0**  **4 ,419**  **3 ,978** 

**2 41.0**  **8 7.8**  **3 ,600**  **3 ,250**  **2 4,000**  **E lectronic**  **0 .65**  **5 8.0**  **4 ,680**  **4 ,225** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­5**

### 5A.2.1.2 8­foot Single Pin Slimline General Service Fluorescent Lamps

Table 5 A.2.5 8­foot T8 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Commercial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**3 60.1**  **9 4.8**  **5 ,697**  **5 ,130**  **1 5,000**  **E lectronic**  **0 .88**  **1 12.8**  **1 0,028**  **9 ,029** 

**4 60.1**  **9 8.2**  **5 ,902**  **5 ,428**  **1 5,000**  **E lectronic**  **0 .88**  **1 12.8**  **1 0,387**  **9 ,553** 

**5 60.1**  **1 01.5**  **6 ,100**  **5 ,795**  **1 8,000**  **E lectronic**  **0 .88**  **1 12.8**  **1 0,736**  **1 0,199** 

**5 57.0**  **1 01.8**  **5 ,803**  **5 ,450**  **2 4,000**  **E lectronic**  **0 .88**  **1 07.5**  **1 0,213**  **9 ,592** 

**5 55.0**  **1 03.6**  **5 ,698**  **5 ,415**  **1 8,000**  **E lectronic**  **0 .88**  **1 02.0**  **1 0,028**  **9 ,530** 

**3 60.1**  **9 4.8**  **5 ,697**  **5 ,130**  **1 5,000**  **E lectronic**  **0 .85**  **1 09.1**  **9 ,686**  **8 ,721** 

**4 60.1**  **9 8.2**  **5 ,902**  **5 ,428**  **1 5,000**  **E lectronic**  **0 .85**  **1 09.1**  **1 0,033**  **9 ,228** 

**5 60.1**  **1 01.5**  **6 ,100**  **5 ,795**  **1 8,000**  **E lectronic**  **0 .85**  **1 09.1**  **1 0,370**  **9 ,852** 

**5 57.0**  **1 01.8**  **5 ,803**  **5 ,450**  **2 4,000**  **E lectronic**  **0 .85**  **1 06.0**  **9 ,864**  **9 ,265** 

**5 55.0**  **1 03.6**  **5 ,698**  **5 ,415**  **1 8,000**  **E lectronic**  **0 .85**  **9 8.5**  **9 ,687**  **9 ,206** 

**5 57.0**  **1 01.8**  **5,803 5,450**  **2 4,000**  **E lectronic**  **0 .78**  **1 02.5**  **9 ,052**  **8 ,502** 

**3 60.1**  **9 4.8**  **5 ,697**  **5 ,130**  **1 5,000**  **E lectronic**  **0 .78**  **1 00.4**  **8 ,888**  **8 ,003** 

**4 60.1**  **9 8.2**  **5 ,902**  **5 ,428**  **1 5,000**  **E lectronic**  **0 .78**  **1 00.4**  **9 ,207**  **8 ,468** 

**5 60.1**  **1 01.5**  **6 ,100**  **5 ,795**  **1 8,000**  **E lectronic**  **0 .78**  **1 00.4**  **9 ,516**  **9 ,040** 

**5 55.0**  **1 03.6**  **5 ,698**  **5 ,415**  **1 8,000**  **E lectronic**  **0 .78**  **9 0.2**  **8 ,889**  **8 ,447** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­6**

### Table 5A.2.6 8­foot T12 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 75.0**  **8 5.6**  **6 ,420**  **5 ,906**  **1 2,000**  **M agnetic**  **0 .94**  **1 58.0**  **1 2,070**  **1 1,103** 

**1 75.0**  **8 7.3**  **6 ,548**  **6 ,157**  **1 2,000**  **M agnetic**  **0 .94**  **1 58.0**  **1 2,309**  **1 1,575** 

**2 75.0**  **9 2.0**  **6 ,900**  **6 ,370**  **1 5,000**  **M agnetic**  **0 .94**  **1 58.0**  **1 2,972**  **1 1,976** 

**0 75.0**  **8 5.6**  **6 ,420**  **5 ,906**  **1 2,000**  **E lectronic**  **0 .88**  **1 35.0**  **1 1,299**  **1 0,395** 

**1 75.0**  **8 7.3**  **6 ,548**  **6 ,157**  **1 2,000**  **E lectronic**  **0 .88**  **1 35.0**  **1 1,524**  **1 0,836** 

**2 75.0**  **9 2.0**  **6 ,900**  **6 ,370**  **1 5,000**  **E lectronic**  **0 .88**  **1 35.0**  **1 2,144**  **1 1,211** 

**1 60.5**  **8 7.6**  **5 ,300**  **4 ,664**  **1 2,000**  **M agnetic**  **0 .88**  **1 26.0**  **9 ,328**  **8 ,209** 

**2 60.5**  **9 2.6**  **5 ,602**  **5 ,152**  **1 2,000**  **M agnetic**  **0 .88**  **1 26.0**  **9 ,860**  **9 ,068** 

**3 60.5**  **9 7.5**  **5 ,899**  **5 ,480**  **1 5,000**  **M agnetic**  **0 .88**  **1 26.0**  **1 0,382**  **9 ,645** 

**1 60.5**  **8 7.6**  **5 ,300**  **4 ,664**  **1 2,000**  **E lectronic**  **0 .88**  **1 10.0**  **9 ,328**  **8 ,209** 

**2 60.5**  **9 2.6**  **5 ,602**  **5,152 12,000**  **E lectronic**  **0 .88**  **1 10.0**  **9 ,860**  **9 ,068** 

**3 60.5**  **9 7.5**  **5 ,899**  **5 ,480**  **1 5,000**  **E lectronic**  **0 .88**  **1 10.0**  **1 0,382**  **9 ,645** 

**0 75.0**  **8 5.6**  **6 ,420**  **5 ,906**  **1 2,000**  **E lectronic**  **0 .85**  **1 32.0**  **1 0,914**  **1 0,040** 

**1 75.0**  **8 7.3**  **6 ,548**  **6 ,157**  **1 2,000**  **E lectronic**  **0 .85**  **1 32.0**  **1 1,131**  **1 0,467** 

**2 75.0**  **9 2.0**  **6 ,900**  **6 ,370**  **1 5,000**  **E lectronic**  **0 .85**  **1 32.0**  **1 1,730**  **1 0,829** 

**1 60.5**  **8 7.6**  **5 ,300**  **4 ,664**  **1 2,000**  **E lectronic**  **0 .85**  **1 07.0**  **9 ,010**  **7 ,929** 

**2 60.5**  **9 2.6**  **5 ,602**  **5 ,152**  **1 2,000**  **E lectronic**  **0 .85**  **1 07.0**  **9 ,524**  **8 ,758** 

**3 60.5**  **9 7.5**  **5 ,899**  **5 ,480**  **1 5,000**  **E lectronic**  **0 .85**  **1 07.0**  **1 0,028**  **9 ,316** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­7**

### 5A.2.1.3 8­foot Recessed Double Contact High Output General Service

Fluorescent Lamps

Table 5 A.2.7 8­foot T8 Recessed Double Contact High Output 2­Lamps per Ballast Lampand­Ballast Designs in the Industrial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**4 86.0**  **9 1.9**  **7 ,903**  **7 ,100**  **2 4,000**  **E lectronic**  **0 .88**  **1 60.0**  **1 3,910**  **1 2,496** 

**4 86.0**  **9 3.0**  **7 ,998**  **7 ,200**  **1 8,000**  **E lectronic**  **0 .88**  **1 60.0**  **1 4,076**  **1 2,672** 

**5 86.0**  **9 5.3**  **8 ,196**  **7 ,800**  **1 8,000**  **E lectronic**  **0 .88**  **1 60.0**  **1 4,425**  **1 3,728** 

**4 86.0**  **9 1.9**  **7 ,903**  **7 ,100**  **2 4,000**  **E lectronic**  **0 .81**  **1 51.0**  **1 2,804**  **1 1,502** 

**4 86.0**  **9 3.0**  **7 ,998**  **7 ,200**  **1 8,000**  **E lectronic**  **0 .81**  **1 51.0**  **1 2,957**  **1 1,664** 

**5 86.0**  **9 5.3**  **8 ,196**  **7 ,800**  **1 8,000**  **E lectronic**  **0 .81**  **1 51.0**  **1 3,277**  **1 2,636** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­8**

### Table 5A.2.8 8­foot T12 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 113.0**  **8 0.1**  **9 ,051**  **8 ,145**  **1 2,000**  **M agnetic**  **0 .95**  **2 37.0**  **1 7,197**  **1 5,476** 

**1 113.0**  **8 3.2**  **9 ,402**  **8 ,648**  **1 2,000**  **M agnetic**  **0 .95**  **2 37.0**  **1 7,863**  **1 6,431** 

**0 97.0**  **8 2.5**  **8 ,003**  **6 ,950**  **1 2,000**  **M agnetic**  **0 .91**  **2 03.0**  **1 4,565**  **1 3,205** 

**2 97.0**  **8 6.1**  **8 ,352**  **7 ,515**  **1 2,000**  **M agnetic**  **0 .91**  **2 03.0**  **1 5,200**  **1 4,279** 

**3 97.0**  **8 7.6**  **8 ,497**  **7 ,650**  **1 2,000**  **M agnetic**  **0 .91**  **2 03.0**  **1 5,465**  **1 4,535** 

**3 97.0**  **8 8.9**  **8 ,623**  **7 ,750**  **1 2,000**  **M agnetic**  **0 .91**  **2 03.0**  **1 5,694**  **1 4,725** 

**0 113.0**  **8 0.1**  **9 ,051**  **8 ,145**  **1 2,000**  **E lectronic**  **0 .90**  **2 11.5**  **1 6,292**  **1 4,661** 

**1 113.0**  **8 3.2**  **9 ,402**  **8 ,648**  **1 2,000**  **E lectronic**  **0 .90**  **2 11.5**  **1 6,923**  **1 5,566** 

**0 97.0**  **8 2.5**  **8 ,003**  **6 ,950**  **1 2,000**  **E lectronic**  **0 .90**  **1 85.6**  **1 4,405**  **1 2,510** 

**2 97.0**  **8 6.1**  **8 ,352**  **7 ,515**  **1 2,000**  **E lectronic**  **0 .90**  **1 85.6**  **1 5,033**  **1 3,527** 

**3 97.0**  **8 7.6**  **8 ,497**  **7,650 12,000**  **E lectronic**  **0 .90**  **1 85.6**  **1 5,295**  **1 3,770** 

**3 97.0**  **8 8.9**  **8 ,623**  **7 ,750**  **1 2,000**  **E lectronic**  **0 .90**  **1 85.6**  **1 5,522**  **1 3,950** 

**0 113.0**  **8 0.1**  **9 ,051**  **8 ,145**  **1 2,000**  **E lectronic**  **0 .88**  **2 05.4**  **1 5,930**  **1 4,335** 

**1 113.0**  **8 3.2**  **9 ,402**  **8 ,648**  **1 2,000**  **E lectronic**  **0 .88**  **2 05.4**  **1 6,547**  **1 5,220** 

**0 97.0**  **8 2.5**  **8 ,003**  **6 ,950**  **1 2,000**  **E lectronic**  **0 .88**  **1 77.0**  **1 4,084**  **1 2,232** 

**2 97.0**  **8 6.1**  **8 ,352**  **7 ,515**  **1 2,000**  **E lectronic**  **0 .88**  **1 77.0**  **1 4,699**  **1 3,226** 

**3 97.0**  **8 7.6**  **8 ,497**  **7 ,650**  **1 2,000**  **E lectronic**  **0 .88**  **1 77.0**  **1 4,955**  **1 3,464** 

**3 97.0**  **8 8.9**  **8 ,623**  **7 ,750**  **1 2,000**  **E lectronic**  **0 .88**  **1 77.0**  **1 5,177**  **1 3,640** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­9**

### 5A.2.1.4 4­foot T5 Miniature Bipin Standard Output General Service Fluorescent

Lamps

Table 5 A.2.9 4­foot T5 Miniature Bipin Standard Output 2­Lamps per Ballast Lamp­andBallast Designs in the Commercial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 27.8**  **8 6.0**  **2 ,391**  **1 ,650**  **2 0,000**  **E lectronic**  **1 .15**  **7 0.7**  **5 ,499**  **3 ,795** 

**1 27.8**  **1 04.3**  **2 ,900**  **2 ,660**  **2 0,000**  **E lectronic**  **1 .15**  **7 0.7**  **6 ,669**  **6 ,118** 

**2 27.8**  **1 09.7**  **3 ,050**  **2 ,898**  **2 0,000**  **E lectronic**  **1 .15**  **7 0.7**  **7 ,014**  **6 ,665** 

**2 26.0**  **1 11.5**  **2 ,899**  **2 ,660**  **2 5,000**  **E lectronic**  **1 .15**  **6 7.5**  **6 ,668**  **6 ,118** 

**0 27.8**  **8 6.0**  **2 ,391**  **1 ,650**  **2 0,000**  **E lectronic**  **1 .00**  **6 3.6**  **4 ,782**  **3 ,300** 

**1 27.8**  **1 04.3**  **2 ,900**  **2 ,660**  **2 0,000**  **E lectronic**  **1 .00**  **6 3.6**  **5 ,799**  **5 ,320** 

**2 27.8**  **1 09.7**  **3 ,050**  **2 ,898**  **2 0,000**  **E lectronic**  **1 .00**  **6 3.6**  **6 ,099**  **5 ,796** 

**2 26.0**  **1 11.5**  **2 ,899**  **2 ,660**  **2 5,000**  **E lectronic**  **1 .00**  **5 9.6**  **5 ,798**  **5 ,320** 

**0 27.8**  **8 6.0**  **2 ,391**  **1 ,650**  **2 0,000**  **E lectronic**  **0 .90**  **5 8.9**  **4 ,303**  **2 ,970** 

**1 27.8**  **1 04.3**  **2 ,900**  **2 ,660**  **2 0,000**  **E lectronic**  **0 .90**  **5 8.9**  **5 ,219**  **4 ,788** 

**2 27.8**  **1 09.7**  **3,050 2,898**  **2 0,000**  **E lectronic**  **0 .90**  **5 8.9**  **5 ,489**  **5 ,216** 

**2 26.0**  **1 11.5**  **2 ,899**  **2 ,660**  **2 5,000**  **E lectronic**  **0 .90**  **5 4.4**  **5 ,218**  **4 ,788** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­10**

### 5A.2.1.5 4­foot T5 Miniature Bipin High Output General Service Fluorescent

Lamps

Table 5 A.2.10 4­foot T5 Miniature Bipin High Output 2­Lamps per Ballast Lamp­andBallast Designs in the Industrial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 53.8**  **7 6.0**  **4 ,089**  **2 ,885**  **2 0,000**  **E lectronic**  **1 .00**  **1 20.0**  **8 ,178**  **5 ,770** 

**1 51.0**  **9 8.0**  **4 ,998**  **4 ,600**  **2 5,000**  **E lectronic**  **1 .00**  **1 17.0**  **9 ,996**  **9 ,200** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­11**

### 5A.2.2 Systems Used by Consumers of T12 Electronic Ballasts

5A.2.2.1 4 ­foot Medium Bipin General Service Fluorescent Lamps

Table 5A.2.11 4­foot T8 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Industrial SectorsEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .75**  **7 5.3**  **6 ,750**  **6 ,413** 

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .88**  **8 6.8**  **7 ,920**  **7 ,524** 

**4 26.6**  **9 3.0**  **2 ,475**  **2 ,350**  **3 0,000**  **E lectronic**  **1 .18**  **8 7.7**  **8 ,762**  **8 ,319** 

**4 26.6**  **9 3.0**  **2 ,475**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .88**  **6 6.5**  **6 ,534**  **6 ,204** 

**4 30.4**  **9 3.8**  **2 ,850**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .78**  **7 2.2**  **6 ,669**  **6 ,271** 

**4 30.4**  **9 3.8**  **2 ,850**  **2 ,680**  **2 0,000**  **E lectronic**  **1 .00**  **9 0.3**  **8 ,550**  **8 ,040** 

**5 32.5**  **9 5.4**  **3 ,100**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .71**  **7 1.7**  **6 ,603**  **6 ,209** 

**5 32.5**  **9 5.4**  **3 ,100**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .88**  **8 6.8**  **8 ,184**  **7 ,696** 

**5 28.4**  **9 6.0**  **2 ,725**  **2 ,560**  **1 8,000**  **E lectronic**  **1 .00**  **8 4.0**  **8 ,175**  **7 ,680** 

**5 28.4**  **9 6.0**  **2 ,725**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .78**  **6 7.0**  **6 ,377**  **5 ,990** 

***** **Al l**  **s ystems**  **use 3**  **lamps per**  **ballast.**



### Table 5A.2.12 4­foot T12 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Industrial SectorsEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 41.0**  **7 8.0**  **3 ,200**  **2 ,880**  **2 0,000**  **E lectronic**  **0 .88**  **1 07.7**  **8 ,448**  **7 ,603** 

**0 34.0**  **7 7.9**  **2 ,650**  **2 ,300**  **2 0,000**  **E lectronic**  **0 .88**  **9 1.7**  **6 ,996**  **6 ,072** 

***** **Al l**  **s ystems**  **use 3**  **lamps per**  **ballast.**

**5A­12**

### Table 5A.2.13 4­foot T8 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Residential SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**4 32.5**  **9 2.3**  **3 ,000**  **2 ,850**  **2 4,000**  **E lectronic**  **0 .75**  **4 9.6**  **4 ,500**  **4 ,275** 

**4 26.6**  **9 3.0**  **2 ,475**  **2 ,350**  **3 0,000**  **E lectronic**  **0 .78**  **4 0.5**  **3 ,861**  **3 ,666** 

**4 30.4**  **9 3.8**  **2 ,850**  **2 ,680**  **2 0,000**  **E lectronic**  **0 .75**  **4 7.2**  **4 ,275**  **4 ,020** 

**5 32.5**  **9 5.4**  **3 ,100**  **2 ,915**  **2 4,000**  **E lectronic**  **0 .71**  **4 6.8**  **4 ,402**  **4 ,139** 

**5 28.4**  **9 6.0**  **2 ,725**  **2 ,560**  **1 8,000**  **E lectronic**  **0 .78**  **4 5.6**  **4 ,251**  **3 ,994** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**



### Table 5A.2.14 4­foot T12 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Residential SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 41.0**  **7 6.8**  **3 ,150**  **2 ,860**  **1 5,000**  **E lectronic**  **0 .65**  **5 8.0**  **4 ,095**  **3 ,718** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­13**

### 5A.2.2.2 8­foot Single Pin Slimline General Service Fluorescent Lamps

Table 5 A.2.15 8­foot T8 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Commercial and Industrial SectorsEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**4 60.1**  **9 8.2**  **5 ,900**  **5 ,428**  **1 5,000**  **E lectronic**  **0 .78**  **1 00.4**  **9 ,204**  **8 ,468** 

**5 60.1**  **1 01.5**  **6 ,100**  **5 ,795**  **1 8,000**  **E lectronic**  **0 .88**  **1 12.8**  **1 0,736**  **1 0,199** 

**5 60.1**  **1 01.5**  **6 ,100**  **5 ,795**  **1 8,000**  **E lectronic**  **0 .78**  **1 00.4**  **9 ,516**  **9 ,040** 

**5 57.0**  **1 01.8**  **5 ,800**  **5 ,450**  **2 4,000**  **E lectronic**  **0 .78**  **1 02.5**  **9 ,048**  **8 ,502** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**



### Table 5A.2.16 8­foot T12 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial and Industrial SectorsEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 75.0**  **8 5.6**  **6 ,420**  **5 ,906**  **1 2,000**  **E lectronic**  **0 .88**  **1 35.0**  **1 1,299**  **1 0,395** 

**1 60.5**  **8 7.6**  **5 ,300**  **4 ,664**  **1 2,000**  **E lectronic**  **0 .88**  **1 10.0**  **9 ,328**  **8 ,209** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­14**

### 5A.2.2.3 8­foot Recessed Double Contact High Output General Service

Fluorescent Lamps

Table 5 A.2.17 8­foot T8 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**4 86.0**  **9 1.9**  **7 ,900**  **7 ,100**  **2 4,000**  **E lectronic**  **0 .88**  **1 60.0**  **1 3,904**  **1 2,496** 

**4 86.0**  **9 3.0**  **8 ,000**  **7 ,200**  **1 8,000**  **E lectronic**  **0 .88**  **1 60.0**  **1 4,080**  **1 2,672** 

**5 86.0**  **9 5.3**  **8 ,200**  **7 ,800**  **1 8,000**  **E lectronic**  **0 .88**  **1 60.0**  **1 4,432**  **1 3,728** 

**5 86.0**  **9 5.3**  **8 ,200**  **7 ,800**  **1 8,000**  **E lectronic**  **0 .81**  **1 51.0**  **1 3,284**  **1 2,636** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**



### Table 5A.2.18 8­foot T12 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial SectorEfficacyLevelRatedWattageRatedEfficacyInitialLightOutputMeanLightOutputLifeBallastTypeBallastFactorSystemPowerRating*SystemInitialLightOutputSystemMeanLightOutputWlm/WlmlmhrWlmlm

**0 113.0**  **8 0.1**  **9 ,050**  **8 ,145**  **1 2,000**  **E lectronic**  **0 .90**  **2 11.5**  **1 6,290**  **1 4,661** 

**0 97.0**  **8 2.5**  **8 ,000**  **6 ,950**  **1 2,000**  **E lectronic**  **0 .90**  **1 85.6**  **1 4,400**  **1 2,510** 

***** **Al l**  **s ystems**  **use 2**  **lamps per**  **ballast.**

**5A­15**

### 5A.3 INCANDESCENT REFLECTOR LAMPS

**The f**  **ollowing tables**  **list the**  **lamp designs**  **used in**  **the shipments**  **analysis and**  **NIA for** 

**incandescent reflector**  **lamps (IRL).**  **In addition**  **to the**  **lamp designs**  **considered in**  **the LCC**  **and**

**1** 

### PBP **analysis, the**  **shipments analysis**  **and NIA**  **include 65W**  **BR30 IRL that**  **are exempt**  **from**

**coverage. The**  **shipments analysis**  **and NIA**  **also allow**  **users to**  **include reflector**  **CFL in**  **the**

**analysis.**

Table 5 A.3.1 90W PAR38 Incandescent Reflector Lamps

EL 2 Design

Option Lamp

D escriptor Wattage I ni tial

L ight

Output Mean

L ight

Output Effi cacy L amp

L ife

W lm lm lm/W h r

**0 Hal**  **ogen P**  **AR38 3**  **90.0 1,310**  **1 ,277**  **1 4.6**  **2 ,500** 

**1 Improved** 

**H alogen** 

**(Xenon) PAR38**  **8 5.7**  **1 ,310**  **1 ,277**  **1 5.3**  **2 ,500** 

**1 Improved** 

**H alogen** 

**(Xenon) PAR38**  **9 0.0**  **1 ,396**  **1 ,361**  **1 5.5**  **2 ,500** 

**2 Long**  **L ife**  **HIR PAR38**  **8 2.5**  **1 ,310**  **1 ,277**  **1 5.9**  **6 ,000** 

**2 Long**  **L ife**  **HIR PAR38**  **9 0.0**  **1 ,470**  **1 ,433**  **1 6.3**  **6 ,000** 

**2 Improved** 

**H alogen** 

**(Silver) PAR38**  **7 9.0**  **1 ,310**  **1 ,277**  **1 6.6**  **3 ,000** 

**3 Improved** 

**H alogen** 

**(Silver) PAR38**  **7 0.0**  **1 ,260**  **1 ,229**  **1 8.0**  **3 ,000** 

**3 HIR**  **P AR38**  **1 00.0**  **2 ,030**  **1 ,979**  **2 0.3**  **3 ,000** 

**4 HIR**  **P AR38**  **6 6.0**  **1 ,310**  **1 ,277**  **1 9.8**  **4 ,000** 

**4 Improved**  **H IR**  **PAR38 9**  **0.0 2**  **,030 1**  **,979 2**  **2.6 4**  **,000**

**I mproved**  **H IR**  **Reflector C**  **FL 26.0**  **1 ,300**  **1 ,040**  **5 0.0**  **8 ,000** 

**5 Refl**  **ector C**  **FL PAR38**  **6 0.0**  **1 ,260**  **1 ,229**  **2 1.0**  **4 ,200** 

**5 Improved**  **H IR** 

**Plus PAR38**  **9 0.0**  **2 ,217**  **2 ,162**  **2 4.6**  **4 ,200** 

**1 BR**  **stands for**  **“Bulged Reflector.”** 

**2 EL**  **stands for**  **“Efficacy Level.”** 

**3 PAR**  **stands for**  **“Parabolic Aluminized**  **Reflector.”**

**5A­16**

### Table 5A.3.2 75W PAR38 Incandescent Reflector Lamps

EL Desi gn

O ption Lamp

D escriptor Wattage I ni tial

L ight

Output Mean

L ight

Output Effi cacy L amp

L ife

W lm lm lm/W h r

**0 Hal**  **ogen P**  **AR38 7**  **5.0 1**  **,050 1**  **,024 1**  **4.0 2**  **,500**

**1 Improved** 

**H alogen** 

**(Xenon) PAR38**  **7 1.7**  **1 ,050**  **1 ,024**  **1 4.6**  **2 ,500** 

**1 Improved** 

**H alogen** 

**(Xenon) PAR38**  **7 5.0**  **1 ,103**  **1 ,075**  **1 4.7**  **2 ,500** 

**2 Long**  **L ife**  **HIR PAR38**  **6 8.8**  **1 ,050**  **1 ,024**  **1 5.3**  **6 ,000** 

**2 Long**  **L ife**  **HIR PAR38**  **8 8.0**  **1 ,470**  **1 ,433**  **1 6.7**  **6 ,000** 

**2 Improved** 

**H alogen** 

**(Silver) PAR38**  **6 6.0**  **1 ,050**  **1 ,024**  **1 5.9**  **3 ,000** 

**2 Improved** 

**H alogen** 

**(Silver) PAR38**  **7 9.0**  **1 ,310**  **1 ,277**  **1 6.6**  **3 ,000** 

**3 HIR**  **P AR38**  **6 0.0**  **1 ,050**  **1 ,024**  **1 7.5**  **3 ,000** 

**3 HIR**  **P AR38**  **8 0.0**  **1 ,500**  **1 ,463**  **1 8.8**  **3 ,000** 

**4 Improved**  **H IR**  **PAR38 5**  **5.0 1**  **,050 1**  **,024 1**  **9.1 4**  **,000**

**4 Improved**  **H IR**  **PAR38 9**  **0.0 2**  **,030 1**  **,979 2**  **2.6 4**  **,000**

**R efl**  **ector C**  **FL Reflector**  **C FL**  **23.0 1**  **,200 9**  **60 5**  **2.2 8**  **,000**

**5 Improved**  **H IR** 

**Plus PAR38**  **5 1.7**  **1 ,050**  **1 ,024**  **2 0.3**  **4 ,200** 

**5 Improved**  **H IR** 

**Plus PAR38**  **8 3.0**  **2 ,030**  **1 ,979**  **2 4.5**  **4 ,200** 

**5 A­17** 

### Table 5A.3.3 50W PAR30 Incandescent Reflector Lamps

EL Desi gn

O ption Lamp

D escriptor Wattage I ni tial

L ight

Output Mean

L ight

Output Effi cacy L amp

L ife

W lm lm lm/W h r

**B R30** 

**I ncandescent** 

**IRL BR30** 

**I ncandescent**  **65.0 6**  **20 5**  **64 9**  **.5 2**  **,000**

**0 Hal**  **ogen P**  **AR30 5**  **0.0 6**  **30 6**  **14 1**  **2.6 3**  **,000**

**1 Improved** 

**H alogen** 

**(Xenon) PAR30**  **4 7.8**  **6 30**  **6 14**  **1 3.2**  **3 ,000** 

**1 Improved** 

**H alogen** 

**(Xenon) PAR30**  **5 0.0**  **6 62**  **6 45**  **1 3.2**  **3 ,000** 

**2 Long**  **L ife**  **HIR PAR30**  **4 6.0**  **6 20**  **6 05**  **1 3.5**  **6 ,000** 

**2 Long**  **L ife**  **HIR PAR30**  **5 0.0**  **6 95**  **6 78**  **1 3.9**  **6 ,000** 

**2 Improved** 

**H alogen** 

**(Silver) PAR30**  **4 5.0**  **6 30**  **6 14**  **1 4.0**  **3 ,000** 

**2 Improved** 

**H alogen** 

**(Silver) PAR30**  **5 0.0**  **7 20**  **7 02**  **1 4.4**  **3 ,000** 

**3 HIR**  **P AR30**  **4 1.8**  **6 30**  **6 14**  **1 5.1**  **3 ,000** 

**3 HIR**  **P AR30**  **5 0.0**  **8 25**  **8 04**  **1 6.5**  **4 ,000** 

**4 Improved**  **H IR**  **PAR30 4**  **0.0 6**  **80 6**  **63 1**  **7.0 4**  **,000**

**4 Improved**  **H IR**  **PAR30 5**  **0.0 9**  **00 8**  **78 1**  **8.0 3**  **,000**

**R efl**  **ector C**  **FL Reflector**  **C FL**  **16.0 7**  **50 6**  **00 4**  **6.9 8**  **,000**

**5 Improved**  **H IR** 

**Plus PAR30**  **4 0.0**  **7 65**  **7 46**  **1 9.1**  **4 ,200** 

**5 Improved**  **H IR** 

**Plus PAR30**  **5 0.0**  **1 ,014**  **9 89**  **2 0.3**  **4 ,200** 

**5 A­18**