APPENDIX 5A. ENGINEERING RESULTS USED IN THE SHIPMENTS,

NATIONAL IMPACTS, AND LIFE­CYCLE COST SUBGROUP ANALYSES

TABLE OF CONTENTS

5A.1 INTRODUCTION .................................................................................................. 5A­1

5A.2 GENERAL SERVICE FLUORESCENT LAMPS................................................. 5A­1

5A.2.1 Systems Used in the Shipments Analysis and NIA .................................... 5A­1

5A.2.1.1 4­foot Medium Bipin General Service Fluorescent Lamps............ 5A­2

5A.2.1.2 8­foot Single Pin Slimline General Service Fluorescent Lamps .... 5A­6

5A.2.1.3 8­foot Recessed Double Contact High Output General Service

Fluorescent Lamps.......................................................................... 5A­8

5A.2.1.4 4­foot T5 Miniature Bipin Standard Output General Service

Fluorescent Lamps........................................................................ 5A­10

5A.2.1.5 4­foot T5 Miniature Bipin High Output General Service

Fluorescent Lamps........................................................................ 5A­11

5A.2.2 Systems Used by Consumers of T12 Electronic Ballasts......................... 5A­12

5A.2.2.1 4­foot Medium Bipin General Service Fluorescent Lamps.......... 5A­12

5A.2.2.2 8­foot Single Pin Slimline General Service Fluorescent Lamps .. 5A­14

5A.2.2.3 8­foot Recessed Double Contact High Output General Service

Fluorescent Lamps........................................................................ 5A­15

5A.3 INCANDESCENT REFLECTOR LAMPS.......................................................... 5A­16

LIST OF TABLES

Table 5A.2.1 4­foot T8 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial Sector................................................................................ 5A­2

Table 5A.2.2 4­foot T12 Medium Bipin Lamp­and­Ballast Designs in the Commercial

Sector .......................................................................................................... 5A­3

Table 5A.2.3 4­foot T8 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Residential Sector...................................................... 5A­3

Table 5A.2.4 4­foot T12 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Residential Sector ............................................................................. 5A­5

Table 5A.2.5 8­foot T8 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial Sector.............................................................. 5A­6

Table 5A.2.6 8­foot T12 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial Sector.............................................................. 5A­7

Table 5A.2.7 8­foot T8 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector .................................... 5A­8

Table 5A.2.8 8­foot T12 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector .................................... 5A­9

Table 5A.2.9 4­foot T5 Miniature Bipin Standard Output 2­Lamps per Ballast Lampand­Ballast Designs in the Commercial Sector ........................................ 5A­10

Table 5A.2.10 4­foot T5 Miniature Bipin High Output 2­Lamps per Ballast Lamp­andBallast Designs in the Industrial Sector.................................................... 5A­11

5A­i

EE-2006-STD-0131 COMMENT 37.2
Table 5A.2.11 4­foot T8 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs

in the Commercial and Industrial Sectors................................................. 5A­12

Table 5A.2.12 4­foot T12 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs

in the Commercial and Industrial Sectors................................................. 5A­12

Table 5A.2.13 4­foot T8 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Residential Sector ........................................................................... 5A­13

Table 5A.2.14 4­foot T12 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Residential Sector ........................................................................... 5A­13

Table 5A.2.15 8­foot T8 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial and Industrial Sectors................................... 5A­14

Table 5A.2.16 8­foot T12 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial and Industrial Sectors................................... 5A­14

Table 5A.2.17 8­foot T8 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector .................................. 5A­15

Table 5A.2.18 8­foot T12 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector .................................. 5A­15

Table 5A.3.1 90W PAR38 Incandescent Reflector Lamps ................................................... 5A­16

Table 5A.3.2 75W PAR38 Incandescent Reflector Lamps ................................................... 5A­17

Table 5A.3.3 50W PAR30 Incandescent Reflector Lamps ................................................... 5A­18

5A­ii

EE-2006-STD-0131 COMMENT 37.2
APPENDIX 5A. ENGINEERING RESULTS USED IN THE SHIPMENTS, NATIONAL

IMPACTS, AND LIFE­CYCLE COST SUBGROUP ANALYSES

5A.1 INTRODUCTION

This appendix presents the engineering results used in the shipments analysis, national

impacts analysis (NIA), and life­cycle cost (LCC) subgroup analysis. In addition to many of the

lamp and lamp­and­ballast designs considered in the primary LCC and payback period (PBP)

analysis, the shipments analysis and national impact analysis (NIA) includes designs that do not

save energy or do not emit lumens within 10 percent of the baseline lamp­and­ballast system.

Product substitutions like reflector compact fluorescent lamps (CFL) that are not included in the

LCC and PBP analysis are also considered in the NIA and shipments analysis. Furthermore, the

LCC subgroup analysis contains an assessment of LCC and PBP results for consumers of

fluorescent T12 electronic baseline lamp­and­ballast systems, and the engineering results for

those systems are presented in this appendix.

5A.2 GENERAL SERVICE FLUORESCENT LAMPS

5A.2.1 Systems Used in the Shipments Analysis and NIA

The following tables list the lamp­and­ballast designs used in the general service

fluorescent lamp (GSFL) shipments analysis and the NIA. In addition to many of the lamp­andballast designs considered in the LCC and PBP analysis, the shipments analysis and NIA include

designs that do not save energy or do not emit lumens within 10 percent of the baseline lampand­ballast system.

5A­1

EE-2006-STD-0131 COMMENT 37.2
5A.2.1.1 4­foot Medium Bipin General Service Fluorescent Lamps

Table 5A.2.1 4­foot T8 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.88 86.8 7,396 6,653

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.88 86.8 7,791 7,154

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.88 86.8 7,919 7,524

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.88 86.8 8,185 7,696

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.88 80.4 7,528 7,075

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.88 69.7 7,198 6,758

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.88 66.5 6,531 6,204

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.78 77.9 6,556 5,897

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.78 77.9 6,905 6,341

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.78 77.9 7,019 6,669

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.78 77.9 7,255 6,821

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.78 72.2 6,673 6,271

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.78 67.0 6,380 5,990

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.78 59.4 5,789 5,499

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.71 71.7 5,967 5,368

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.71 71.7 6,286 5,772

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.71 71.7 6,389 6,071

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.71 71.7 6,604 6,209

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.71 66.4 6,074 5,708

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.71 61.6 5,807 5,453

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.71 54.5 5,269 5,006

* All systems use 3 lamps per ballast.

5A­2

EE-2006-STD-0131 COMMENT 37.2
Table 5A.2.2 4­foot T12 Medium Bipin Lamp­and­Ballast Designs in the Commercial

SectorEfficacy Level

Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 41.0 78.0 3,198 2,880 20,000 Magnetic 0.95 129.0 9,114 8,208

1 41.0 80.5 3,301 3,000 20,000 Magnetic 0.95 129.0 9,406 8,550

1 41.0 82.9 3,399 3,060 24,000 Magnetic 0.95 129.0 9,687 8,721

2 41.0 87.8 3,600 3,250 24,000 Magnetic 0.95 129.0 10,259 9,263

0 34.0 77.9 2,649 2,300 20,000 Magnetic 0.88 108.0 6,992 6,072

1 34.0 82.4 2,802 2,460 20,000 Magnetic 0.88 108.0 7,396 6,494

2 34.0 85.3 2,900 2,610 20,000 Magnetic 0.88 108.0 7,657 6,890

3 34.0 91.2 3,101 2,790 24,000 Magnetic 0.88 108.0 8,186 7,366

0 41.0 78.0 3,198 2,880 20,000 Electronic 0.88 107.7 8,443 7,603

1 41.0 80.5 3,301 3,000 20,000 Electronic 0.88 107.7 8,713 7,920

1 41.0 82.9 3,399 3,060 24,000 Electronic 0.88 107.7 8,973 8,078

2 41.0 87.8 3,600 3,250 24,000 Electronic 0.88 107.7 9,503 8,580

0 34.0 77.9 2,649 2,300 20,000 Electronic 0.88 91.7 6,992 6,072

1 34.0 82.4 2,802 2,460 20,000 Electronic 0.88 91.7 7,396 6,494

2 34.0 85.3 2,900 2,610 20,000 Electronic 0.88 91.7 7,657 6,890

3 34.0 91.2 3,101 2,790 24,000 Electronic 0.88 91.7 8,186 7,366

0 41.0 78.0 3,198 2,880 20,000 Electronic 0.86 106.3 8,251 7,430

1 41.0 80.5 3,301 3,000 20,000 Electronic 0.86 106.3 8,515 7,740

1 41.0 82.9 3,399 3,060 24,000 Electronic 0.86 106.3 8,769 7,895

2 41.0 87.8 3,600 3,250 24,000 Electronic 0.86 106.3 9,287 8,385

0 34.0 77.9 2,649 2,300 20,000 Electronic 0.86 90.3 6,833 5,934

1 34.0 82.4 2,802 2,460 20,000 Electronic 0.86 90.3 7,228 6,347

2 34.0 85.3 2,900 2,610 20,000 Electronic 0.86 90.3 7,483 6,734

3 34.0 91.2 3,101 2,790 24,000 Electronic 0.86 90.3 8,000 7,198

* All electronic systems use 3 lamps per ballast. All magnetic systems use a 2­lamp ballast and a 1­lamp ballast.

Table 5A.2.3 4­foot T8 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Residential Sector

5A­3

EE-2006-STD-0131 COMMENT 37.2
Efficacy Level

Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.88 58.6 4,931 4,435

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.88 58.6 5,194 4,770

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.88 58.6 5,280 5,016

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.88 58.6 5,457 5,130

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.88 54.6 5,019 4,717

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.88 51.2 4,798 4,506

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.88 45.4 4,354 4,136

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.78 51.6 4,370 3,931

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.78 51.6 4,604 4,228

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.78 51.6 4,680 4,446

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.78 51.6 4,837 4,547

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.78 48.9 4,448 4,181

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.78 45.6 4,253 3,994

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.78 40.5 3,859 3,666

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.71 46.8 3,978 3,578

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.71 46.8 4,190 3,848

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.71 46.8 4,260 4,047

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.71 46.8 4,403 4,139

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.71 44.9 4,049 3,806

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.71 41.7 3,871 3,635

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.71 37.0 3,513 3,337

* All systems use 2 lamps per ballast.

5A­4

EE-2006-STD-0131 COMMENT 37.2
Table 5A.2.4 4­foot T12 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Residential Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

1 34.0 82.4 2,802 2,460 20,000 Electronic 0.75 48.0 4,202 3,690

2 34.0 85.3 2,900 2,610 20,000 Electronic 0.75 48.0 4,350 3,915

3 34.0 91.2 3,101 2,790 24,000 Electronic 0.75 48.0 4,651 4,185

0 41.0 76.8 3,149 2,860 15,000 Magnetic 0.68 70.0 4,282 3,890

0 41.0 80.5 3,301 3,000 20,000 Magnetic 0.68 70.0 4,489 4,080

1 41.0 82.9 3,399 3,060 24,000 Magnetic 0.68 70.0 4,623 4,162

2 41.0 87.8 3,600 3,250 24,000 Magnetic 0.68 70.0 4,896 4,420

1 34.0 82.4 2,802 2,460 20,000 Magnetic 0.66 60.0 3,698 3,247

2 34.0 85.3 2,900 2,610 20,000 Magnetic 0.66 60.0 3,828 3,445

3 34.0 91.2 3,101 2,790 24,000 Magnetic 0.66 60.0 4,093 3,683

0 41.0 76.8 3,149 2,860 15,000 Electronic 0.65 58.0 4,093 3,718

0 41.0 80.5 3,301 3,000 20,000 Electronic 0.65 58.0 4,291 3,900

1 41.0 82.9 3,399 3,060 24,000 Electronic 0.65 58.0 4,419 3,978

2 41.0 87.8 3,600 3,250 24,000 Electronic 0.65 58.0 4,680 4,225

* All systems use 2 lamps per ballast.

5A­5

EE-2006-STD-0131 COMMENT 37.2
5A.2.1.2 8­foot Single Pin Slimline General Service Fluorescent Lamps

Table 5A.2.5 8­foot T8 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Commercial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

3 60.1 94.8 5,697 5,130 15,000 Electronic 0.88 112.8 10,028 9,029

4 60.1 98.2 5,902 5,428 15,000 Electronic 0.88 112.8 10,387 9,553

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.88 112.8 10,736 10,199

5 57.0 101.8 5,803 5,450 24,000 Electronic 0.88 107.5 10,213 9,592

5 55.0 103.6 5,698 5,415 18,000 Electronic 0.88 102.0 10,028 9,530

3 60.1 94.8 5,697 5,130 15,000 Electronic 0.85 109.1 9,686 8,721

4 60.1 98.2 5,902 5,428 15,000 Electronic 0.85 109.1 10,033 9,228

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.85 109.1 10,370 9,852

5 57.0 101.8 5,803 5,450 24,000 Electronic 0.85 106.0 9,864 9,265

5 55.0 103.6 5,698 5,415 18,000 Electronic 0.85 98.5 9,687 9,206

5 57.0 101.8 5,803 5,450 24,000 Electronic 0.78 102.5 9,052 8,502

3 60.1 94.8 5,697 5,130 15,000 Electronic 0.78 100.4 8,888 8,003

4 60.1 98.2 5,902 5,428 15,000 Electronic 0.78 100.4 9,207 8,468

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.78 100.4 9,516 9,040

5 55.0 103.6 5,698 5,415 18,000 Electronic 0.78 90.2 8,889 8,447

* All systems use 2 lamps per ballast.

5A­6

EE-2006-STD-0131 COMMENT 37.2
Table 5A.2.6 8­foot T12 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 75.0 85.6 6,420 5,906 12,000 Magnetic 0.94 158.0 12,070 11,103

1 75.0 87.3 6,548 6,157 12,000 Magnetic 0.94 158.0 12,309 11,575

2 75.0 92.0 6,900 6,370 15,000 Magnetic 0.94 158.0 12,972 11,976

0 75.0 85.6 6,420 5,906 12,000 Electronic 0.88 135.0 11,299 10,395

1 75.0 87.3 6,548 6,157 12,000 Electronic 0.88 135.0 11,524 10,836

2 75.0 92.0 6,900 6,370 15,000 Electronic 0.88 135.0 12,144 11,211

1 60.5 87.6 5,300 4,664 12,000 Magnetic 0.88 126.0 9,328 8,209

2 60.5 92.6 5,602 5,152 12,000 Magnetic 0.88 126.0 9,860 9,068

3 60.5 97.5 5,899 5,480 15,000 Magnetic 0.88 126.0 10,382 9,645

1 60.5 87.6 5,300 4,664 12,000 Electronic 0.88 110.0 9,328 8,209

2 60.5 92.6 5,602 5,152 12,000 Electronic 0.88 110.0 9,860 9,068

3 60.5 97.5 5,899 5,480 15,000 Electronic 0.88 110.0 10,382 9,645

0 75.0 85.6 6,420 5,906 12,000 Electronic 0.85 132.0 10,914 10,040

1 75.0 87.3 6,548 6,157 12,000 Electronic 0.85 132.0 11,131 10,467

2 75.0 92.0 6,900 6,370 15,000 Electronic 0.85 132.0 11,730 10,829

1 60.5 87.6 5,300 4,664 12,000 Electronic 0.85 107.0 9,010 7,929

2 60.5 92.6 5,602 5,152 12,000 Electronic 0.85 107.0 9,524 8,758

3 60.5 97.5 5,899 5,480 15,000 Electronic 0.85 107.0 10,028 9,316

* All systems use 2 lamps per ballast.

5A­7

EE-2006-STD-0131 COMMENT 37.2
5A.2.1.3 8­foot Recessed Double Contact High Output General Service

Fluorescent Lamps

Table 5A.2.7 8­foot T8 Recessed Double Contact High Output 2­Lamps per Ballast Lampand­Ballast Designs in the Industrial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

4 86.0 91.9 7,903 7,100 24,000 Electronic 0.88 160.0 13,910 12,496

4 86.0 93.0 7,998 7,200 18,000 Electronic 0.88 160.0 14,076 12,672

5 86.0 95.3 8,196 7,800 18,000 Electronic 0.88 160.0 14,425 13,728

4 86.0 91.9 7,903 7,100 24,000 Electronic 0.81 151.0 12,804 11,502

4 86.0 93.0 7,998 7,200 18,000 Electronic 0.81 151.0 12,957 11,664

5 86.0 95.3 8,196 7,800 18,000 Electronic 0.81 151.0 13,277 12,636

* All systems use 2 lamps per ballast.

5A­8

EE-2006-STD-0131 COMMENT 37.2
Table 5A.2.8 8­foot T12 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 113.0 80.1 9,051 8,145 12,000 Magnetic 0.95 237.0 17,197 15,476

1 113.0 83.2 9,402 8,648 12,000 Magnetic 0.95 237.0 17,863 16,431

0 97.0 82.5 8,003 6,950 12,000 Magnetic 0.91 203.0 14,565 13,205

2 97.0 86.1 8,352 7,515 12,000 Magnetic 0.91 203.0 15,200 14,279

3 97.0 87.6 8,497 7,650 12,000 Magnetic 0.91 203.0 15,465 14,535

3 97.0 88.9 8,623 7,750 12,000 Magnetic 0.91 203.0 15,694 14,725

0 113.0 80.1 9,051 8,145 12,000 Electronic 0.90 211.5 16,292 14,661

1 113.0 83.2 9,402 8,648 12,000 Electronic 0.90 211.5 16,923 15,566

0 97.0 82.5 8,003 6,950 12,000 Electronic 0.90 185.6 14,405 12,510

2 97.0 86.1 8,352 7,515 12,000 Electronic 0.90 185.6 15,033 13,527

3 97.0 87.6 8,497 7,650 12,000 Electronic 0.90 185.6 15,295 13,770

3 97.0 88.9 8,623 7,750 12,000 Electronic 0.90 185.6 15,522 13,950

0 113.0 80.1 9,051 8,145 12,000 Electronic 0.88 205.4 15,930 14,335

1 113.0 83.2 9,402 8,648 12,000 Electronic 0.88 205.4 16,547 15,220

0 97.0 82.5 8,003 6,950 12,000 Electronic 0.88 177.0 14,084 12,232

2 97.0 86.1 8,352 7,515 12,000 Electronic 0.88 177.0 14,699 13,226

3 97.0 87.6 8,497 7,650 12,000 Electronic 0.88 177.0 14,955 13,464

3 97.0 88.9 8,623 7,750 12,000 Electronic 0.88 177.0 15,177 13,640

* All systems use 2 lamps per ballast.

5A­9

EE-2006-STD-0131 COMMENT 37.2
5A.2.1.4 4­foot T5 Miniature Bipin Standard Output General Service Fluorescent

Lamps

Table 5A.2.9 4­foot T5 Miniature Bipin Standard Output 2­Lamps per Ballast Lamp­andBallast Designs in the Commercial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 27.8 86.0 2,391 1,650 20,000 Electronic 1.15 70.7 5,499 3,795

1 27.8 104.3 2,900 2,660 20,000 Electronic 1.15 70.7 6,669 6,118

2 27.8 109.7 3,050 2,898 20,000 Electronic 1.15 70.7 7,014 6,665

2 26.0 111.5 2,899 2,660 25,000 Electronic 1.15 67.5 6,668 6,118

0 27.8 86.0 2,391 1,650 20,000 Electronic 1.00 63.6 4,782 3,300

1 27.8 104.3 2,900 2,660 20,000 Electronic 1.00 63.6 5,799 5,320

2 27.8 109.7 3,050 2,898 20,000 Electronic 1.00 63.6 6,099 5,796

2 26.0 111.5 2,899 2,660 25,000 Electronic 1.00 59.6 5,798 5,320

0 27.8 86.0 2,391 1,650 20,000 Electronic 0.90 58.9 4,303 2,970

1 27.8 104.3 2,900 2,660 20,000 Electronic 0.90 58.9 5,219 4,788

2 27.8 109.7 3,050 2,898 20,000 Electronic 0.90 58.9 5,489 5,216

2 26.0 111.5 2,899 2,660 25,000 Electronic 0.90 54.4 5,218 4,788

* All systems use 2 lamps per ballast.

5A­10

EE-2006-STD-0131 COMMENT 37.2
5A.2.1.5 4­foot T5 Miniature Bipin High Output General Service Fluorescent

Lamps

Table 5A.2.10 4­foot T5 Miniature Bipin High Output 2­Lamps per Ballast Lamp­andBallast Designs in the Industrial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 53.8 76.0 4,089 2,885 20,000 Electronic 1.00 120.0 8,178 5,770

1 51.0 98.0 4,998 4,600 25,000 Electronic 1.00 117.0 9,996 9,200

* All systems use 2 lamps per ballast.

5A­11

EE-2006-STD-0131 COMMENT 37.2
5A.2.2 Systems Used by Consumers of T12 Electronic Ballasts

5A.2.2.1 4­foot Medium Bipin General Service Fluorescent Lamps

Table 5A.2.11 4­foot T8 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Industrial Sectors Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.75 75.3 6,750 6,413

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.88 86.8 7,920 7,524

4 26.6 93.0 2,475 2,350 30,000 Electronic 1.18 87.7 8,762 8,319

4 26.6 93.0 2,475 2,350 30,000 Electronic 0.88 66.5 6,534 6,204

4 30.4 93.8 2,850 2,680 20,000 Electronic 0.78 72.2 6,669 6,271

4 30.4 93.8 2,850 2,680 20,000 Electronic 1.00 90.3 8,550 8,040

5 32.5 95.4 3,100 2,915 24,000 Electronic 0.71 71.7 6,603 6,209

5 32.5 95.4 3,100 2,915 24,000 Electronic 0.88 86.8 8,184 7,696

5 28.4 96.0 2,725 2,560 18,000 Electronic 1.00 84.0 8,175 7,680

5 28.4 96.0 2,725 2,560 18,000 Electronic 0.78 67.0 6,377 5,990

* All systems use 3 lamps per ballast.

Table 5A.2.12 4­foot T12 Medium Bipin 3­Lamps per Ballast Lamp­and­Ballast Designs in

the Commercial and Industrial Sectors Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 41.0 78.0 3,200 2,880 20,000 Electronic 0.88 107.7 8,448 7,603

0 34.0 77.9 2,650 2,300 20,000 Electronic 0.88 91.7 6,996 6,072

* All systems use 3 lamps per ballast.

5A­12

EE-2006-STD-0131 COMMENT 37.2
Table 5A.2.13 4­foot T8 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Residential Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.75 49.6 4,500 4,275

4 26.6 93.0 2,475 2,350 30,000 Electronic 0.78 40.5 3,861 3,666

4 30.4 93.8 2,850 2,680 20,000 Electronic 0.75 47.2 4,275 4,020

5 32.5 95.4 3,100 2,915 24,000 Electronic 0.71 46.8 4,402 4,139

5 28.4 96.0 2,725 2,560 18,000 Electronic 0.78 45.6 4,251 3,994

* All systems use 2 lamps per ballast.

Table 5A.2.14 4­foot T12 Medium Bipin 2­Lamps per Ballast Lamp­and­Ballast Designs in

the Residential Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 41.0 76.8 3,150 2,860 15,000 Electronic 0.65 58.0 4,095 3,718

* All systems use 2 lamps per ballast.

5A­13

EE-2006-STD-0131 COMMENT 37.2
5A.2.2.2 8­foot Single Pin Slimline General Service Fluorescent Lamps

Table 5A.2.15 8­foot T8 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast Designs

in the Commercial and Industrial Sectors Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

4 60.1 98.2 5,900 5,428 15,000 Electronic 0.78 100.4 9,204 8,468

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.88 112.8 10,736 10,199

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.78 100.4 9,516 9,040

5 57.0 101.8 5,800 5,450 24,000 Electronic 0.78 102.5 9,048 8,502

* All systems use 2 lamps per ballast.

Table 5A.2.16 8­foot T12 Single Pin Slimline 2­Lamps per Ballast Lamp­and­Ballast

Designs in the Commercial and Industrial Sectors Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 75.0 85.6 6,420 5,906 12,000 Electronic 0.88 135.0 11,299 10,395

1 60.5 87.6 5,300 4,664 12,000 Electronic 0.88 110.0 9,328 8,209

* All systems use 2 lamps per ballast.

5A­14

EE-2006-STD-0131 COMMENT 37.2
5A.2.2.3 8­foot Recessed Double Contact High Output General Service

Fluorescent Lamps

Table 5A.2.17 8­foot T8 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

4 86.0 91.9 7,900 7,100 24,000 Electronic 0.88 160.0 13,904 12,496

4 86.0 93.0 8,000 7,200 18,000 Electronic 0.88 160.0 14,080 12,672

5 86.0 95.3 8,200 7,800 18,000 Electronic 0.88 160.0 14,432 13,728

5 86.0 95.3 8,200 7,800 18,000 Electronic 0.81 151.0 13,284 12,636

* All systems use 2 lamps per ballast.

Table 5A.2.18 8­foot T12 Recessed Double Contact High Output 2­Lamps per Ballast

Lamp­and­Ballast Designs in the Industrial Sector Efficacy Level Rated

Wattage

Rated

Efficacy

Initial

Light

Output

Mean

Light

Output

Life

Ballast

Type

Ballast

Factor

System

Power

Rating*

System Initial

Light Output

System

Mean

Light Output

W

lm/

W

lmlm

hr

W

lmlm

0 113.0 80.1 9,050 8,145 12,000 Electronic 0.90 211.5 16,290 14,661

0 97.0 82.5 8,000 6,950 12,000 Electronic 0.90 185.6 14,400 12,510

* All systems use 2 lamps per ballast.

5A­15

EE-2006-STD-0131 COMMENT 37.2
5A.3 INCANDESCENT REFLECTOR LAMPS

The following tables list the lamp designs used in the shipments analysis and NIA for

incandescent reflector lamps (IRL). In addition to the lamp designs considered in the LCC and

1 PBP analysis, the shipments analysis and NIA include 65W BR30 IRL that are exempt from

coverage. The shipments analysis and NIA also allow users to include reflector CFL in the

analysis.

Table 5A.3.1 90W PAR38 Incandescent Reflector Lamps

EL2 Design

Option

Lamp

Descriptor

Wattage

Initial

Light

Output

Mean

Light

Output

Efficacy

Lamp

Life

W lm lm lm/W hr

0 Halogen PAR383 90.0 1,310 1,277 14.6 2,500

1

Improved

Halogen

(Xenon)

PAR38 85.7 1,310 1,277 15.3 2,500

1

Improved

Halogen

(Xenon)

PAR38 90.0 1,396 1,361 15.5 2,500

2 Long Life HIR PAR38 82.5 1,310 1,277 15.9 6,000

2 Long Life HIR PAR38 90.0 1,470 1,433 16.3 6,000

2

Improved

Halogen

(Silver)

PAR38 79.0 1,310 1,277 16.6 3,000

3

Improved

Halogen

(Silver)

PAR38 70.0 1,260 1,229 18.0 3,000

3 HIR PAR38 100.0 2,030 1,979 20.3 3,000

4 HIR PAR38 66.0 1,310 1,277 19.8 4,000

4 Improved HIR PAR38 90.0 2,030 1,979 22.6 4,000

Improved HIR Reflector CFL 26.0 1,300 1,040 50.0 8,000

5 Reflector CFL PAR38 60.0 1,260 1,229 21.0 4,200

5 Improved HIR

Plus PAR38 90.0 2,217 2,162 24.6 4,200

1 BR stands for “Bulged Reflector.”

2 EL stands for “Efficacy Level.”

3 PAR stands for “Parabolic Aluminized Reflector.”

5A­16

EE-2006-STD-0131 COMMENT 37.2
Table 5A.3.2 75W PAR38 Incandescent Reflector Lamps

EL Design

Option

Lamp

Descriptor

Wattage

Initial

Light

Output

Mean

Light

Output

Efficacy

Lamp

Life

W lm lm lm/W hr

0 Halogen PAR38 75.0 1,050 1,024 14.0 2,500

1 Improved

Halogen

(Xenon)

PAR38 71.7 1,050 1,024 14.6 2,500

1 Improved

Halogen

(Xenon)

PAR38 75.0 1,103 1,075 14.7 2,500

2 Long Life HIR PAR38 68.8 1,050 1,024 15.3 6,000

2 Long Life HIR PAR38 88.0 1,470 1,433 16.7 6,000

2 Improved

Halogen

(Silver)

PAR38 66.0 1,050 1,024 15.9 3,000

2 Improved

Halogen

(Silver)

PAR38 79.0 1,310 1,277 16.6 3,000

3 HIR PAR38 60.0 1,050 1,024 17.5 3,000

3 HIR PAR38 80.0 1,500 1,463 18.8 3,000

4 Improved HIR PAR38 55.0 1,050 1,024 19.1 4,000

4 Improved HIR PAR38 90.0 2,030 1,979 22.6 4,000

Reflector CFL Reflector CFL 23.0 1,200 960 52.2 8,000

5 Improved HIR

Plus PAR38 51.7 1,050 1,024 20.3 4,200

5 Improved HIR

Plus PAR38 83.0 2,030 1,979 24.5 4,200

5A­17

EE-2006-STD-0131 COMMENT 37.2
Table 5A.3.3 50W PAR30 Incandescent Reflector Lamps

EL Design

Option

Lamp

Descriptor

Wattage

Initial

Light

Output

Mean

Light

Output

Efficacy

Lamp

Life

W lm lm lm/W hr

BR30

Incandescent

IRL

BR30

Incandescent 65.0 620 564 9.5 2,000

0 Halogen PAR30 50.0 630 614 12.6 3,000

1 Improved

Halogen

(Xenon)

PAR30 47.8 630 614 13.2 3,000

1 Improved

Halogen

(Xenon)

PAR30 50.0 662 645 13.2 3,000

2 Long Life HIR PAR30 46.0 620 605 13.5 6,000

2 Long Life HIR PAR30 50.0 695 678 13.9 6,000

2 Improved

Halogen

(Silver)

PAR30 45.0 630 614 14.0 3,000

2 Improved

Halogen

(Silver)

PAR30 50.0 720 702 14.4 3,000

3 HIR PAR30 41.8 630 614 15.1 3,000

3 HIR PAR30 50.0 825 804 16.5 4,000

4 Improved HIR PAR30 40.0 680 663 17.0 4,000

4 Improved HIR PAR30 50.0 900 878 18.0 3,000

Reflector CFL Reflector CFL 16.0 750 600 46.9 8,000

5 Improved HIR

Plus PAR30 40.0 765 746 19.1 4,200

5 Improved HIR

Plus PAR30 50.0 1,014 989 20.3 4,200

5A­18

EE-2006-STD-0131 COMMENT 37.2