### Name: Jim Ward

Title: EHS Manager Company: Red Hills Power Plant Sign Date: 8/2/2010 Name: Jeremy Hutchens Title: Senior Project Manager Company: Alliance Source Testing, LLC Sign Date: 8/2/2010 Permitted Facility Representative / Date Testing Company Representative / Date



## GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 10, 2011 Page 1 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010 Facility Information: Red Hills Generating Facility
2391 Pensacola Road
PO Box 358
Ackerman MS 39735
Contact: Jim Ward
Phone: (662) 387-4175, ext. 234
Fax:
Email: jim.ward@gdfsuezna.com Testing Company: Alliance Source Testing, LLC
214 Central Circle SW

Decatur AL 35603
Contact: Jeremy Hutchens
Phone: (256) 260-3974
Fax: (256) 351-0151
Email: jeremy.hutchens@stacktest.com

Air Permit Number: 55076 Permitted Source ID/Name: Boiler No. 2 AA002
Permitted Maximum Process Rate: 1,600-1,800 KPPH Max. Normal Operation Process Rate: 1,600-1,800 KPPH Target Process Test Rate 1,600-1,800 KPPH

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: RHPP is a single unit lignite-fueled electrical generation facility that supplies electricity to the Tennessee Valley Authority (TVA) electrical system. Operations at the facility include lignite processing (e.g., conveying, crushing, sizing, and temporary storage of lignite), steam production (e.g., two (2) 250 MW (lignite fueled) Circulating Fluidized Bed (CFB) Boilers), electrical power generation (e.g., 440 MW steam turbine generator), limestone handling and drying, water treatment (e.g., chemical treatment and cooling towers) for process makeup water, handling and onsite disposal of ash. Emissions from each boiler are exhaust from a single common stack. Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description 10100318 External Combustion Boilers - Electric Generation - Lignite - Atmospheric Fluidized Bed Combustion - Circulating Bed

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
Common Stack 216 2160 480 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 180 0 Common Stack Total organic compounds

(TOC) as Propane Method 25A 3 180 0 Common Stack

Filterable PM2.5 OTM - 27/28 3 420 0 Common Stack



### Thursday, February 10, 2011 Page 2 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. The attached test report provides full methodology descriptions.

Organic Condensible Particulate OTM - 27/28 3 420 0 Common Stack

Arsenic Method 29 3 420 0 Common Stack Antimony Method 29 3 420 0 Common Stack Mercury Method 29 3 420 0 Common Stack Beryllium Method 29 3 420 0 Common Stack Cadmium Method 29 3 420 0 Common Stack Chromium Method 29 3 420 0 Common Stack Cobalt Method 29 3 420 0 Common Stack Lead Method 29 3 420 0 Common Stack Manganese Method 29 3 420 0 Common Stack Nickel Method 29 3 420 0 Common Stack Selenium Method 29 3 420 0 Common Stack Filterable Particulate Method 29 3 420 0 Common Stack O2 Method 3A O2 3 180 0 Common Stack Co2 Method 3A CO2 3 180 0 Common Stack Sulfur Dioxide Method 6C 3 180 0 Common Stack Nitrogen oxides (NOx) Method 7E 3 180 0 Common Stack



### Thursday, February 10, 2011 Page 3 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010 Sampling / Stack Data Results Summary



### Location Common Stack - Method 10 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Common Stack - Method 25A Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 4 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 29 Average
Run Number 3 1 2
Test Date 5/21/2010 5/19/2010 5/20/2010
Run Start Time 7:30:00 AM 9:11:00 AM 7:14:00 AM

Run Finish Time 5:22:00 PM 6:09:00 PM 4:34:00 PM Net Run Time, minutes 420 420 420 Dry Gas Meter Volume Sampled, dscf 251.456 248.307 248.090 249.284 Moisture Content of Stack Gas, % 19.25 18.73 19.34 19.107 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 13.8 13.8 13.7 13.767 Oxygen, % 5.3 5.3 5.1 5.233 Average Stack Gas Temperature, °F 304.00 312.08 305.42 307.167 Dry Volumetric Flow Rate, dry scfm 603,310.4 604,095.8 599,460.8 602,289.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,096,099.8 1,101,290.9 1,094,573.0 1,097,321.23 3 Percent Isokinetic of Sampling Rate, % 101.1 99.7 100.4 100.400 F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000
Fw 11950 11950 11950 11,950.000
Fc 1910 1910 1910 1,910.000



### Location Common Stack - Method 3A CO2 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 5 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 3A O2 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Common Stack - Method 6C Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 6 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 7E Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Common Stack - OTM - 27/28 Average
Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 7 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010 Emissions Summary



### Location: Common Stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 6.41E-03 7.28E-03 5.99E-03 0.007 ppm 6.81E+00 7.58E+00 6.24E+00 6.877 ppm@7%O2 5.95E+00 6.75E+00 5.56E+00 6.087



### Location: Common Stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.12E-03 1.28E-03 1.36E-03 0.001 ppm 7.54E-01 8.49E-01 9.02E-01 0.835 ppm@7%O2 6.59E-01 7.56E-01 8.04E-01 0.740



### Location: Common Stack - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.0018 0.00197 0.00199 0.002 lb/mmBtuO2 2.11E-07 2.28E-07 2.30E-07 0.000


### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.00585 0.00672 0.00659 0.006 lb/mmBtuO2 6.86E-07 7.79E-07 7.63E-07 0.000


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.00107 0.0012 0.00133 0.001 lb/mmBtuO2 1.25E-07 1.39E-07 1.54E-07 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.00071 0.00058 0.00058 0.001 lb/mmBtuO2 8.33E-08 6.72E-08 6.72E-08 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.1337 0.0414 0.0381 0.071 lb/mmBtuO2 1.57E-05 4.80E-06 4.41E-06 0.000


### Compound: Cobalt Average RunNumber 1 2 3



### Thursday, February 10, 2011 Page 8 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010 Mass_mg 0.00491 0.00462 0.00433 0.005 lb/mmBtuO2 5.76E-07 5.35E-07 5.01E-07 0.000


### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 135.8 121.2 141.2 132.733 lb/mmBtuO2 1.59E-02 1.40E-02 1.64E-02 0.015


### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.07709 0.01148 0.00988 0.033 lb/mmBtuO2 9.04E-06 1.33E-06 1.14E-06 0.000


### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.2177 0.2179 0.2873 0.241 lb/mmBtuO2 2.55E-05 2.53E-05 3.33E-05 0.000


### Compound: Mercury Average RunNumber 1 2 3 Mass_mg 0.05126 0.12613 0.10086 0.093 lb/mmBtuO2 6.01E-06 1.46E-05 1.17E-05 0.000


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.0111 0.0099 0.0158 0.012 lb/mmBtuO2 1.30E-06 1.15E-06 1.83E-06 0.000


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.046 0.0119 0.0088 0.022 lb/mmBtuO2 5.40E-06 1.38E-06 1.02E-06 0.000



### Location: Common Stack - Method 6C 

### Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 1.41E-01 1.19E-01 1.14E-01 0.125 ppm 6.56E+01 5.42E+01 5.21E+01 57.300 ppm@7%O2 5.73E+01 4.83E+01 4.64E+01 50.667



### Location: Common Stack - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 1 2 3 lb/mmBtuO2 1.03E-01 1.09E-01 1.20E-01 0.111 ppm 6.64E+01 6.94E+01 7.62E+01 70.667


### Thursday, February 10, 2011 Page 9 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Process Run Data ppm@7%O2 5.80E+01 6.18E+01 6.79E+01 62.567



### Location: Common Stack - OTM - 27/28 Compound: Filterable PM2.5 Average RunNumber 1 2 3 Mass_mg 7.1 7.3 5.3 6.567 lb/mmBtuO2 1.55E-03 1.62E-03 1.21E-03 0.001


### Compound: Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 80.4 19.9 25.8 42.033 lb/mmBtuO2 1.75E-02 4.41E-03 5.91E-03 0.009



### Thursday, February 10, 2011 Page 10 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 Coal Firing Rate 478 tons/hr 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 3 Coal Firing Rate 482 tons/hr 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

4 Coal Firing Rate 480 tons/hr 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Coal Firing Rate 468 tons/hr 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Coal Firing Rate 473 tons/hr 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0



### 7 Coal Firing Rate 445 tons/hr 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Steam Output 3384 1000 lbs/hr 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

3 Steam Output 3365 1000 lbs/hr 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

4 Steam Output 3421 1000 lbs/hr 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 5 Steam Output 3311 1000 lbs/hr 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

Thursday, February 10, 2011 Page 11 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010
6 Steam Output 3387 1000 lbs/hr 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0

7 Steam Output 3257 1000 lbs/hr 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0



### 1 Average Heat Input 4946 MMBtu/hr 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

3 Average Heat Input 4960 MMBtu/hr 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 4 Average Heat Input 4694 MMBtu/hr 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Average Heat Input 4872 MMBtu/hr 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Average Heat Input 4468 MMBtu/hr 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0

7 Average Heat Input 4529 MMBtu/hr 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Sorbent Type and Sorbent Injection Rate (if applicable) 4.84 tons/hr 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 3 Sorbent Type and Sorbent Injection Rate (if applicable) 5.77 tons/hr 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

4 Sorbent Type and Sorbent Injection Rate (if applicable) 5.53 tons/hr 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### Thursday, February 10, 2011 Page 12 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010
5 Sorbent Type and Sorbent Injection Rate (if applicable) 5.89 tons/hr 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Sorbent Type and Sorbent Injection Rate (if applicable) 6.81 tons/hr 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0



### 7 Sorbent Type and Sorbent Injection Rate (if applicable) 3.97 tons/hr 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Unit Net Electric Generation 431 MWh 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

3 Unit Net Electric Generation 432 MWh 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

4 Unit Net Electric Generation 433 MWh 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 5 Unit Net Electric Generation 427 MWh 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Unit Net Electric Generation 432 MWh 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0

7 Unit Net Electric Generation 419 MWh 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Flue Gas Oxygen Content 5 % 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

3 Flue Gas Oxygen Content 5.3 % 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### Thursday, February 10, 2011 Page 13 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010
4 Flue Gas Oxygen Content 5.3 % 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 5 Flue Gas Oxygen Content 5.3 % 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Flue Gas Oxygen Content 5.1 % 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0

7 Flue Gas Oxygen Content 5.3 % 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0



### 1 Flue Gas Carbon Dioxide Content 13.4 % 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

3 Flue Gas Carbon Dioxide Content 13.8 % 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 4 Flue Gas Carbon Dioxide Content 14.1 % 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Flue Gas Carbon Dioxide Content 13.8 % 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Flue Gas Carbon Dioxide Content 13.7 % 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0

7 Flue Gas Carbon Dioxide Content 13.8 % 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Unit Gross Electric Output 492 MWh 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### Thursday, February 10, 2011 Page 14 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010
3 Unit Gross Electric Output 486 MWh 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 4 Unit Gross Electric Output 486 MWh 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Unit Gross Electric Output 482 MWh 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0



### 6 Unit Gross Electric Output 484 MWh 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0

7 Unit Gross Electric Output 476 MWh 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Flue Gas Flow Rate 583495 dscfm 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 3 Flue Gas Flow Rate 585534 dscfm 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

4 Flue Gas Flow Rate 582393 dscfm 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Flue Gas Flow Rate 604108 dscfm 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Flue Gas Flow Rate 599519 dscfm 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0



### 7 Flue Gas Flow Rate 603297 dscfm 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

Thursday, February 10, 2011 Page 15 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010
1 Flue Gas Temperature 308 F 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 3 Flue Gas Temperature 312 F 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

4 Flue Gas Temperature 312 F 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Flue Gas Temperature 312 F 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Flue Gas Temperature 305 F 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0



### 7 Flue Gas Temperature 304 F 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0

1 Flue Gas Moisture Content 19 % 5/18/10, 8:28 AM - 11:45 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

3 Flue Gas Moisture Content 18.7 % 5/18/10, 12:21 PM - 3:34 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0



### 4 Flue Gas Moisture Content 19.1 % 5/18/10, 4:10 PM - 7:23 PM,HCl, HF, HCN, CO, Nox, THC, Methane, HCOH 0

5 Flue Gas Moisture Content 18.7 % 5/19/10, 9:11 AM - 6:09 PM, Metals, PM 0

6 Flue Gas Moisture Content 19.3 % 5/20/10, 7:14 AM - 4:34 PM, Metals, PM 0



### Thursday, February 10, 2011 Page 16 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

APCD Run Data

Process Lab Run Data 7 Flue Gas Moisture Content 19.3 % 5/20-21/10, 7:30 AM - 5:22 AM, Metals, PM 0



### Run Name Value UOM Comments Target Value 1 BAGHOUSE 0 0

Run Name Value UOM Comments 

### 1 Fuel Higher Heating Value 0 Btu/lb 1 Fuel Moisture 0 % 1 Fuel Mercury Content 0 ppm 

### 1 Fuel Cadmium Content 0 ppm 1 Ultimate/Proximate Analysis 0 1 Fuel Nickel Content 0 ppm 1 Fuel Arsenic Content 0 ppm 

### 1 Fuel Chromium Content 0 ppm 1 Fuel Beryllium Content 0 ppm 1 Fuel Lead Content 0 ppm 

### 1 Fuel Manganese 0 ppm 1 Fuel Chlorine Content 0 ppm 1 Fuel Fluorine Content 0 ppm



### Thursday, February 10, 2011 Page 17 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010
Sampling / Stack Data Results Detail



### Location Common Stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 18 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 19 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 29 Average Run Number 3 1 2 Test Date 5/21/2010 5/19/2010 5/20/2010 Run Start Time 7:30:00 AM 9:11:00 AM 7:14:00 AM Run Finish Time 5:22:00 PM 6:09:00 PM 4:34:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 420 420 420 Nozzle Diameter, inches 0.214 0.214 0.214 0.214 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.021 1.021 1.021 1.021 Barometric Pressure, inches of Mercury 29.53 29.55 29.47 29.517 Average Orifice Meter Differential, inches H2O 1.36 1.37 1.36 1.363 Dry Gas Meter Volume Sampled, cubic feet 250.875 252.050 248.890 250.605 Average Dry Gas Meter Temperature, °F 72.63 82.29 74.50 76.473 Dry Gas Meter Volume Sampled, dscf 251.456 248.307 248.090 249.284 Total Moisture Liquid collected, g 1273.7 1215.7 1263.4 1,250.933 Volume of Water Vapor, standard cubic feet 59.95 57.22 59.47 58.880 Moisture Content of Stack Gas, % 19.25 18.73 19.34 19.107 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8075 0.8127 0.8066 0.809 Carbon Dioxide, % 13.8 13.8 13.7 13.767 Oxygen, % 5.3 5.3 5.1 5.233 Carbon Monoxide & Nitrogen, % 80.9 80.9 81.2 81.000 Fuel Factor 1.13 1.13 1.15 Dry Molecular Weight, lb/lb-Mole 30.42 30.42 30.40 30.413 Wet Molecular weight, lb/lb-Mole 28.03 28.09 28.00 28.040 Flue Gas Static Pressure, inches of H2O -0.25 -0.25 -0.25 -0.250 Absolute Flue Gas Pressure, inches of Mercury 29.51 29.53 29.45 29.497 Average Stack Gas Temperature, °F 304.00 312.08 305.42 307.167 Average Velocity Head, inches of H2O 1.0819393441 1265 1.084035892

19294 1.073674229

41376 1.080

Average Stack Gas Velocity, feet/second 71.79 72.13 71.69 71.870 Stack Cross-Sectional Area, square feet 254.469 254.469 254.469 254.469 Dry Volumetric Flow Rate, dry scfm 603,310.4 604,095.8 599,460.8 602,289.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,096,099.8 1,101,290.9 1,094,573.0 1,097,321.2 33 Percent Isokinetic of Sampling Rate, % 101.1 99.7 100.4 100.400 Percent Excess Air, % 33.0 33.0 31.2 32.400 F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000 Round Duct Diameter, inches 216 216 216 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 11950 11950 11950 11,950.000 Fc 1910 1910 1910 1,910.000



### Thursday, February 10, 2011 Page 20 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 3A CO2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 21 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 3A O2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 22 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 23 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 24 of 25

### GDF Suez/RHPP - Ackerman, MS - 2010 Power MACT ICR

8/2/2010

Location Common Stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 25 of 25