Name: Lois A. Knowlson

Title: Senior Environmental Engineer

Company: PSEG Fossil

Sign Date: 9/30/2010

Name: Anthony Fortunato

Title: Senior Testing Supervisor

Company: PSEG Maplewood Testing Services

Sign Date: 9/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

PSEG Sewaren Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 22, 2011 Page 1 of 46
PSEG Sewaren Unit 1

9/30/2010

Facility Information:

PSEG Sewaren Generating Station

751 Cliff Road

Sewaren NJ 07077

Contact: Joseph D. Krejsa

Phone:

Fax:

Email: joseph.krejsa@pseg.com

Testing Company:

Maplewood Testing Services

200 Boyden Avenue

Maplewood NJ 07040

Contact: Anthony Fortunato

Phone: 973-761-1005

Fax: 973-761-1015

Email: anthony.fortunato2@pseg.com

Air Permit Number:

2411 - NJDEP PI 18068 BOP080001

Permitted Source ID/Name:

U1 Sewaren Unit 1

Permitted Maximum Process Rate:

1550 MMBtu/hr

Max. Normal Operation Process Rate:

1550 MMBtu/hr

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Fuel oil fired (alternate natural gas) electric generating utility

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #: 110000801614

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 14.833 157.7 157.7 14.833 487 1579 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Regulation Description Compound Limit Unit

NJAC 7:27-4.2a Total Particulate 335 lb/hr

NJAC 7:27-27.7(a) (Based on annual weighted average of 

all valid stack emission tests performed for four 

consecutive quarters weighted by MW-hr)

Mercury 3 mg/MW-hr

Tuesday, February 22, 2011 Page 2 of 46
PSEG Sewaren Unit 1

9/30/2010

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Filterable Particulate OTM - 27/28 3 240 0

Stack Exit Total PM2.5 OTM - 27/28 3 240 0

Organic Condensible 

Particulate

Stack Exit OTM - 27/28 3 240 0

Stack Exit Filterable PM2.5 OTM - 27/28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit OTM - 27/28 3 240 0

Tuesday, February 22, 2011 Page 3 of 46
PSEG Sewaren Unit 1

9/30/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

As per ICR, potassium permanganate impingers were not used as Hg was measured using Method 30B.

Stack Exit Total Particulate OTM - 27/28 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Cobalt Method 29 3 240 0

Stack Exit O2 Method 3A O2 3 120 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit Total Particulate Method 5/OTM-28 3 240 0

Stack Exit Filterable Particulate Method 5/OTM-28 3 240 0

Organic Condensible 

Particulate

Stack Exit Method 5/OTM-28 3 240 0

Stack Exit Filterable Particulate Method 5 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit Method 5/OTM-28 3 240 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Tuesday, February 22, 2011 Page 4 of 46
PSEG Sewaren Unit 1

9/30/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:20:00 AM 11:01:00 

AM

1:55:00 PM

Run Finish Time 10:35:00 AM 1:18:00 PM 4:17:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 81.459 82.627 84.185 82.757

Moisture Content of Stack Gas, % 5.67 5.62 5.56 5.617

Moisture Saturation at Stack Gas Temperature, % 87.05 90.10 96.11 91.087

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Average Stack Gas Temperature, °F 204.79 206.38 209.63 206.933

Dry Volumetric Flow Rate, dry scfm 273,988.8 276,768.6 281,468.8 277,408.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 368,168.3 373,349.3 380,913.7 374,143.767

Percent Isokinetic of Sampling Rate, % 95.9 96.3 96.5 96.233

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 10

Average

Run Number 1-1 1-2 1-3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:21:00 AM 11:02:00 

AM

1:56:00 PM

Run Finish Time 10:26:00 AM 1:01:00 PM 3:55:00 PM

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4 258,298.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 5 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 7/13/2010 7/14/2010 7/15/2010

Run Start Time 4:15:00 AM 5:52:00 

AM

4:24:00 AM

Run Finish Time 8:00:00 PM 9:35:00 PM 8:08:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 318.031 318.560 327.311 321.301

Moisture Content of Stack Gas, % 5.98 5.73 5.69 5.800

Moisture Saturation at Stack Gas Temperature, % 81.90 84.08 84.71 83.563

Carbon Dioxide, % 4.368 4.3 4.164 4.277

Oxygen, % 15.051 15.111 15.308 15.157

Average Stack Gas Temperature, °F 201.88 203.29 203.75 202.973

Dry Volumetric Flow Rate, dry scfm 269,247.0 267,786.6 274,234.8 270,422.800

Actual Wet Volumetric Flue Gas Flow Rate, acfm 360,914.7 357,806.1 365,785.0 361,501.933

Percent Isokinetic of Sampling Rate, % 97.3 98.0 96.3 97.200

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 25A

Average

Run Number 1-1 1-2 1-3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:21:00 AM 11:02:00 

AM

1:56:00 PM

Run Finish Time 10:26:00 AM 1:01:00 PM 3:55:00 PM

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Dry Volumetric Flow Rate, dry scfm 273988.8 276768600

00

281468.8 9,225,805,15

2.533

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 6 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 7/13/2010 7/15/2010 7/15/2010

Run Start Time 5:16:00 PM 5:03:00 PM 6:23:00 PM

Run Finish Time 6:27:00 PM 6:12:00 PM 7:32:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 40.392 40.937 41.085 40.805

Moisture Content of Stack Gas, % 8.72 6.51 10.64 8.623

Moisture Saturation at Stack Gas Temperature, % 85.48 89.36 88.01 87.617

Carbon Dioxide, % 4.4 4.3 4.3 4.333

Oxygen, % 15 15.1 15.1 15.067

Average Stack Gas Temperature, °F 203.88 206.29 205.54 205.237

Dry Volumetric Flow Rate, dry scfm 269,064.2 271,280.3 263,326.2 267,890.233

Actual Wet Volumetric Flue Gas Flow Rate, acfm 373,245.7 367,028.4 372,313.1 370,862.400

Percent Isokinetic of Sampling Rate, % 98.9 97.4 100.7 99.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 7/13/2010 7/14/2010 7/14/2010

Run Start Time 10:39:00 AM 7:37:00 

AM

2:50:00 PM

Run Finish Time 3:59:00 PM 12:52:00 

PM

8:11:00 PM

Net Run Time, minutes 300 300 300

Dry Gas Meter Volume Sampled, dscf 197.362 200.864 196.485 198.237

Moisture Content of Stack Gas, % 6.63 6.22 5.96 6.270

Moisture Saturation at Stack Gas Temperature, % 78.30 83.27 80.75 80.773

Carbon Dioxide, % 4.341 4.339 4.315 4.332

Oxygen, % 15.124 15.091 15.072 15.096

Average Stack Gas Temperature, °F 199.38 202.67 201.21 201.087

Dry Volumetric Flow Rate, dry scfm 270,422.7 274,231.5 268,506.4 271,053.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 366,095.8 369,100.9 359,360.4 364,852.367

Percent Isokinetic of Sampling Rate, % 96.2 96.5 96.4 96.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 7 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 6C

Average

Run Number 1-1 1-2 1-3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:21:00 AM 11:02:00 

AM

1:56:00 PM

Run Finish Time 10:26:00 AM 1:01:00 PM 3:55:00 PM

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4 258,298.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 6C 3

Average

Run Number 3-1 3-2 3-3

Test Date 7/13/2010 7/15/2010 7/15/2010

Run Start Time 5:18:00 PM 5:04:00 PM 6:23:00 PM

Run Finish Time 6:24:00 PM 6:03:00 PM 7:22:00 PM

Carbon Dioxide, % 4.4 4.3 4.3 4.333

Oxygen, % 15 15.1 15.1 15.067

Dry Volumetric Flow Rate, dry scfm 252456.3 245857.5 238787.9 245,700.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 4.83 6.51 10.64 7.327

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 8 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 7E

Average

Run Number 3-1 3-2 3-3

Test Date 7/13/2010 7/15/2010 7/15/2010

Run Start Time 5:18:00 PM 5:04:00 PM 6:23:00 PM

Run Finish Time 6:24:00 PM 6:03:00 PM 7:22:00 PM

Carbon Dioxide, % 4.4 4.3 4.3 4.333

Oxygen, % 15 15.1 15.1 15.067

Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4 258,298.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 7/13/2010 7/14/2010 7/14/2010

Run Start Time 10:39:00 AM 7:37:00 

AM

2:50:00 PM

Run Finish Time 4:40:00 PM 1:21:00 PM 8:37:00 PM

Net Run Time, minutes 335.42 330.1 330.63

Dry Gas Meter Volume Sampled, dscf 128.624 123.396 128.119 126.713

Moisture Content of Stack Gas, % 6.46 6.03 6.07 6.187

Moisture Saturation at Stack Gas Temperature, % 96.80 94.08 100.00 96.960

Carbon Dioxide, % 4.341 4.339 4.315 4.332

Oxygen, % 15.124 15.091 15.072 15.096

Average Stack Gas Temperature, °F 209.75 208.67 214.25 210.890

Dry Volumetric Flow Rate, dry scfm 273,497.8 263,453.0 270,634.2 269,195.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 375,525.4 357,080.7 369,411.7 367,339.267

Percent Isokinetic of Sampling Rate, % 103.6 104.9 105.8 104.767

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 9 of 46
PSEG Sewaren Unit 1

9/30/2010

Emissions Summary

Location: Stack Exit - Method 0011

Compound: Formaldehyde

Average

RunNumber 1 2 3

Mass_mg 0.23 0.12 0.25 0.200

lb/mmBtuO2 2.10E-04 1.10E-04 2.21E-04 0.000

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1-1 1-2 1-3

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

gr/dscf 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 3 2

Mass_mg 0.0000000041 0.0000000024 0.0000000019 0.000

Elb/hr 4.59E-10 2.66E-10 2.11E-10 0.000

gr/dscf 1.99E-13 1.13E-13 9.20E-14 0.000

lb/mmBtuO2 9.33E-13 5.55E-13 4.36E-13 0.000

mg/dscm 4.55E-10 2.59E-10 2.11E-10 0.000

ng/dscm 4.55E-04 2.59E-04 2.11E-04 0.000

ng/dscm@7%O2 1.08E-03 6.44E-04 5.07E-04 0.001

ppm 2.57E-11 1.46E-11 1.19E-11 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 3 2

Mass_mg 0.000000004 0.0000000017 0.000000002 0.000

Elb/hr 4.48E-10 1.88E-10 2.22E-10 0.000

gr/dscf 1.94E-13 8.02E-14 9.69E-14 0.000

lb/mmBtuO2 9.11E-13 3.93E-13 4.59E-13 0.000

mg/dscm 4.44E-10 1.83E-10 2.22E-10 0.000

ng/dscm 4.44E-04 1.83E-04 2.22E-04 0.000

ng/dscm@7%O2 1.06E-03 4.55E-04 5.33E-04 0.001

ppm 2.61E-11 1.08E-11 1.30E-11 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 3 2

Mass_mg 0.0000000033 0.0000000018 0.0000000017 0.000

Elb/hr 3.70E-10 1.99E-10 1.89E-10 0.000

gr/dscf 1.60E-13 8.49E-14 8.24E-14 0.000

lb/mmBtuO2 7.51E-13 4.16E-13 3.90E-13 0.000

Tuesday, February 22, 2011 Page 10 of 46
PSEG Sewaren Unit 1

9/30/2010

mg/dscm 3.66E-10 1.94E-10 1.88E-10 0.000

ng/dscm 3.66E-04 1.94E-04 1.88E-04 0.000

ng/dscm@7%O2 8.70E-04 4.82E-04 4.51E-04 0.001

ppm 2.15E-11 1.14E-11 1.11E-11 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 3 2

Mass_mg 0.0000000065 0.0000000015 0.0000000016 0.000

Elb/hr 7.28E-10 1.66E-10 1.78E-10 0.000

gr/dscf 3.15E-13 7.07E-14 7.75E-14 0.000

lb/mmBtuO2 1.48E-12 3.47E-13 3.67E-13 0.000

mg/dscm 7.22E-10 1.62E-10 1.77E-10 0.000

ng/dscm 7.22E-04 1.62E-04 1.77E-04 0.000

ng/dscm@7%O2 1.72E-03 4.03E-04 4.25E-04 0.001

ppm 4.44E-11 9.96E-12 1.09E-11 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000036 0.0000000017 0.0000000015 0.000

Elb/hr 4.03E-10 1.89E-10 1.66E-10 0.000

gr/dscf 1.75E-13 8.24E-14 7.07E-14 0.000

lb/mmBtuO2 8.19E-13 3.90E-13 3.47E-13 0.000

mg/dscm 4.00E-10 1.88E-10 1.62E-10 0.000

ng/dscm 4.00E-04 1.88E-04 1.62E-04 0.000

ng/dscm@7%O2 9.51E-04 4.51E-04 4.03E-04 0.001

ppm 2.56E-11 1.21E-11 1.04E-11 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000007 0.0000000017 0.0000000016 0.000

Elb/hr 7.84E-10 1.89E-10 1.77E-10 0.000

gr/dscf 3.40E-13 8.24E-14 7.54E-14 0.000

lb/mmBtuO2 1.59E-12 3.90E-13 3.70E-13 0.000

mg/dscm 7.77E-10 1.88E-10 1.73E-10 0.000

ng/dscm 7.77E-04 1.88E-04 1.73E-04 0.000

ng/dscm@7%O2 1.85E-03 4.51E-04 4.30E-04 0.001

ppm 4.78E-11 1.16E-11 1.06E-11 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000035 0.0000000016 0.0000000014 0.000

Elb/hr 3.92E-10 1.78E-10 1.55E-10 0.000

gr/dscf 1.70E-13 7.75E-14 6.60E-14 0.000

lb/mmBtuO2 7.97E-13 3.67E-13 3.24E-13 0.000

mg/dscm 3.89E-10 1.77E-10 1.51E-10 0.000

ng/dscm 3.89E-04 1.77E-04 1.51E-04 0.000

ng/dscm@7%O2 9.24E-04 4.25E-04 3.75E-04 0.001

ppm 2.49E-11 1.14E-11 9.69E-12 0.000

Tuesday, February 22, 2011 Page 11 of 46
PSEG Sewaren Unit 1

9/30/2010

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000065 0.0000000016 0.0000000015 0.000

Elb/hr 7.28E-10 1.78E-10 1.66E-10 0.000

gr/dscf 3.15E-13 7.75E-14 7.07E-14 0.000

lb/mmBtuO2 1.48E-12 3.67E-13 3.47E-13 0.000

mg/dscm 7.22E-10 1.77E-10 1.62E-10 0.000

ng/dscm 7.22E-04 1.77E-04 1.62E-04 0.000

ng/dscm@7%O2 1.72E-03 4.25E-04 4.03E-04 0.001

ppm 4.44E-11 1.09E-11 9.96E-12 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000043 0.000000002 0.0000000017 0.000

Elb/hr 4.82E-10 2.22E-10 1.88E-10 0.000

gr/dscf 2.09E-13 9.69E-14 8.02E-14 0.000

lb/mmBtuO2 9.79E-13 4.59E-13 3.93E-13 0.000

mg/dscm 4.78E-10 2.22E-10 1.83E-10 0.000

ng/dscm 4.78E-04 2.22E-04 1.83E-04 0.000

ng/dscm@7%O2 1.14E-03 5.33E-04 4.55E-04 0.001

ppm 3.06E-11 1.42E-11 1.18E-11 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000083 0.0000000018 0.0000000017 0.000

Elb/hr 9.29E-10 2.00E-10 1.88E-10 0.000

gr/dscf 4.03E-13 8.72E-14 8.02E-14 0.000

lb/mmBtuO2 1.89E-12 4.13E-13 3.93E-13 0.000

mg/dscm 9.22E-10 2.00E-10 1.83E-10 0.000

ng/dscm 9.22E-04 2.00E-04 1.83E-04 0.000

ng/dscm@7%O2 2.19E-03 4.80E-04 4.55E-04 0.001

ppm 6.22E-11 1.35E-11 1.24E-11 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000061 0.0000000019 0.0000000018 0.000

Elb/hr 6.83E-10 2.11E-10 1.99E-10 0.000

gr/dscf 2.96E-13 9.20E-14 8.49E-14 0.000

lb/mmBtuO2 1.39E-12 4.36E-13 4.16E-13 0.000

mg/dscm 6.77E-10 2.11E-10 1.94E-10 0.000

ng/dscm 6.77E-04 2.11E-04 1.94E-04 0.000

ng/dscm@7%O2 1.61E-03 5.07E-04 4.82E-04 0.001

ppm 4.79E-11 1.49E-11 1.37E-11 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.000000009 0.0000000064 0.0000000057 0.000

Elb/hr 1.01E-09 7.12E-10 6.32E-10 0.000

Tuesday, February 22, 2011 Page 12 of 46
PSEG Sewaren Unit 1

9/30/2010

gr/dscf 4.37E-13 3.10E-13 2.69E-13 0.000

lb/mmBtuO2 2.05E-12 1.47E-12 1.32E-12 0.000

mg/dscm 1.00E-09 7.10E-10 6.15E-10 0.000

ng/dscm 1.00E-03 7.10E-04 6.15E-04 0.001

ng/dscm@7%O2 2.38E-03 1.70E-03 1.53E-03 0.002

ppm 6.07E-11 4.31E-11 3.73E-11 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.00000013 0.000000097 0.000000083 0.000

Elb/hr 1.46E-08 1.08E-08 9.20E-09 0.000

gr/dscf 6.31E-12 4.70E-12 3.91E-12 0.000

lb/mmBtuO2 2.96E-11 2.23E-11 1.92E-11 0.000

mg/dscm 1.44E-08 1.08E-08 8.96E-09 0.000

ng/dscm 1.44E-02 1.08E-02 8.96E-03 0.011

ng/dscm@7%O2 3.42E-02 2.59E-02 2.23E-02 0.027

ppm 0.000

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000054 0.00000031 0.00000033 0.000

Elb/hr 6.05E-08 3.45E-08 3.66E-08 0.000

gr/dscf 2.62E-11 1.50E-11 1.56E-11 0.000

lb/mmBtuO2 1.23E-10 7.12E-11 7.63E-11 0.000

mg/dscm 6.00E-08 3.44E-08 3.56E-08 0.000

ng/dscm 6.00E-02 3.44E-02 3.56E-02 0.043

ng/dscm@7%O2 1.43E-01 8.26E-02 8.85E-02 0.105

ppm 0.000

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000044 0.000000032 0.000000025 0.000

Elb/hr 4.93E-09 3.56E-09 2.77E-09 0.000

gr/dscf 2.14E-12 1.55E-12 1.18E-12 0.000

lb/mmBtuO2 1.00E-11 7.35E-12 5.78E-12 0.000

mg/dscm 4.89E-09 3.55E-09 2.70E-09 0.000

ng/dscm 4.89E-03 3.55E-03 2.70E-03 0.004

ng/dscm@7%O2 1.16E-02 8.52E-03 6.71E-03 0.009

ppm 3.26E-10 2.36E-10 1.80E-10 0.000

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000035 0.000000021 0.000000022 0.000

Elb/hr 3.92E-09 2.34E-09 2.44E-09 0.000

gr/dscf 1.70E-12 1.02E-12 1.04E-12 0.000

lb/mmBtuO2 7.97E-12 4.82E-12 5.09E-12 0.000

mg/dscm 3.89E-09 2.33E-09 2.37E-09 0.000

ng/dscm 3.89E-03 2.33E-03 2.37E-03 0.003

ng/dscm@7%O2 9.24E-03 5.59E-03 5.89E-03 0.007

ppm 0.000

Tuesday, February 22, 2011 Page 13 of 46
PSEG Sewaren Unit 1

9/30/2010

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.0000016 0.00000095 0.00000084 0.000

Elb/hr 1.79E-07 1.06E-07 9.31E-08 0.000

gr/dscf 7.76E-11 4.60E-11 3.96E-11 0.000

lb/mmBtuO2 3.64E-10 2.18E-10 1.94E-10 0.000

mg/dscm 1.78E-07 1.05E-07 9.06E-08 0.000

ng/dscm 1.78E-01 1.05E-01 9.06E-02 0.125

ng/dscm@7%O2 4.23E-01 2.52E-01 2.25E-01 0.300

ppm 0.000

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000024 0.000000012 0.00000002 0.000

Elb/hr 2.69E-09 1.33E-09 2.22E-09 0.000

gr/dscf 1.16E-12 5.81E-13 9.43E-13 0.000

lb/mmBtuO2 5.46E-12 2.76E-12 4.63E-12 0.000

mg/dscm 2.67E-09 1.33E-09 2.16E-09 0.000

ng/dscm 2.67E-03 1.33E-03 2.16E-03 0.002

ng/dscm@7%O2 6.35E-03 3.19E-03 5.37E-03 0.005

ppm 0.000

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000041 0.0000000019 0.0000000017 0.000

Elb/hr 4.59E-10 2.11E-10 1.88E-10 0.000

gr/dscf 1.99E-13 9.20E-14 8.02E-14 0.000

lb/mmBtuO2 9.33E-13 4.36E-13 3.93E-13 0.000

mg/dscm 4.55E-10 2.11E-10 1.83E-10 0.000

ng/dscm 4.55E-04 2.11E-04 1.83E-04 0.000

ng/dscm@7%O2 1.08E-03 5.07E-04 4.55E-04 0.001

ppm 2.92E-11 1.35E-11 1.18E-11 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000059 0.0000000019 0.0000000017 0.000

Elb/hr 6.61E-10 2.11E-10 1.88E-10 0.000

gr/dscf 2.86E-13 9.20E-14 8.02E-14 0.000

lb/mmBtuO2 1.34E-12 4.36E-13 3.93E-13 0.000

mg/dscm 6.55E-10 2.11E-10 1.83E-10 0.000

ng/dscm 6.55E-04 2.11E-04 1.83E-04 0.000

ng/dscm@7%O2 1.56E-03 5.07E-04 4.55E-04 0.001

ppm 4.63E-11 1.49E-11 1.30E-11 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000045 0.0000000016 0.0000000022 0.000

Elb/hr 5.04E-10 1.78E-10 2.44E-10 0.000

Tuesday, February 22, 2011 Page 14 of 46
PSEG Sewaren Unit 1

9/30/2010

gr/dscf 2.18E-13 7.75E-14 1.04E-13 0.000

lb/mmBtuO2 1.02E-12 3.67E-13 5.09E-13 0.000

mg/dscm 5.00E-10 1.77E-10 2.37E-10 0.000

ng/dscm 5.00E-04 1.77E-04 2.37E-04 0.000

ng/dscm@7%O2 1.19E-03 4.25E-04 5.89E-04 0.001

ppm 3.73E-11 1.32E-11 1.77E-11 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000055 0.0000000018 0.0000000027 0.000

Elb/hr 6.16E-10 2.00E-10 2.99E-10 0.000

gr/dscf 2.67E-13 8.72E-14 1.27E-13 0.000

lb/mmBtuO2 1.25E-12 4.13E-13 6.25E-13 0.000

mg/dscm 6.11E-10 2.00E-10 2.91E-10 0.000

ng/dscm 6.11E-04 2.00E-04 2.91E-04 0.000

ng/dscm@7%O2 1.45E-03 4.80E-04 7.23E-04 0.001

ppm 4.80E-11 1.57E-11 2.29E-11 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000077 0.0000000048 0.0000000083 0.000

Elb/hr 8.62E-10 5.34E-10 9.20E-10 0.000

gr/dscf 3.74E-13 2.33E-13 3.91E-13 0.000

lb/mmBtuO2 1.75E-12 1.10E-12 1.92E-12 0.000

mg/dscm 8.55E-10 5.32E-10 8.96E-10 0.000

ng/dscm 8.55E-04 5.32E-04 8.96E-04 0.001

ng/dscm@7%O2 2.03E-03 1.28E-03 2.23E-03 0.002

ppm 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000044 0.0000000072 0.0000000032 0.000

Elb/hr 4.93E-10 8.01E-10 3.55E-10 0.000

gr/dscf 2.14E-13 3.49E-13 1.51E-13 0.000

lb/mmBtuO2 1.00E-12 1.65E-12 7.40E-13 0.000

mg/dscm 4.89E-10 7.98E-10 3.45E-10 0.000

ng/dscm 4.89E-04 7.98E-04 3.45E-04 0.001

ng/dscm@7%O2 1.16E-03 1.92E-03 8.58E-04 0.001

ppm 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000059 0.000000042 0.000000067 0.000

Elb/hr 6.61E-09 4.67E-09 7.43E-09 0.000

gr/dscf 2.86E-12 2.03E-12 3.16E-12 0.000

lb/mmBtuO2 1.34E-11 9.64E-12 1.55E-11 0.000

mg/dscm 6.55E-09 4.66E-09 7.23E-09 0.000

ng/dscm 6.55E-03 4.66E-03 7.23E-03 0.006

ng/dscm@7%O2 1.56E-02 1.12E-02 1.80E-02 0.015

ppm 0.000

Tuesday, February 22, 2011 Page 15 of 46
PSEG Sewaren Unit 1

9/30/2010

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000031 0.0000000044 0.0000000032 0.000

Elb/hr 3.47E-10 4.89E-10 3.55E-10 0.000

gr/dscf 1.50E-13 2.13E-13 1.51E-13 0.000

lb/mmBtuO2 7.06E-13 1.01E-12 7.40E-13 0.000

mg/dscm 3.44E-10 4.88E-10 3.45E-10 0.000

ng/dscm 3.44E-04 4.88E-04 3.45E-04 0.000

ng/dscm@7%O2 8.18E-04 1.17E-03 8.58E-04 0.001

ppm 0.000

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000138 0.0000000135 0.0000000166 0.000

Elb/hr 1.55E-09 1.50E-09 1.84E-09 0.000

gr/dscf 6.70E-13 6.54E-13 7.83E-13 0.000

lb/mmBtuO2 3.14E-12 3.10E-12 3.84E-12 0.000

mg/dscm 1.53E-09 1.50E-09 1.79E-09 0.000

ng/dscm 1.53E-03 1.50E-03 1.79E-03 0.002

ng/dscm@7%O2 3.64E-03 3.60E-03 4.45E-03 0.004

ppm 8.02E-11 7.83E-11 9.37E-11 0.000

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000073 0.0000000035 0.0000000037 0.000

Elb/hr 8.18E-10 3.89E-10 4.10E-10 0.000

gr/dscf 3.54E-13 1.70E-13 1.74E-13 0.000

lb/mmBtuO2 1.66E-12 8.04E-13 8.56E-13 0.000

mg/dscm 8.11E-10 3.88E-10 3.99E-10 0.000

ng/dscm 8.11E-04 3.88E-04 3.99E-04 0.001

ng/dscm@7%O2 1.93E-03 9.32E-04 9.92E-04 0.001

ppm 4.39E-11 2.10E-11 2.16E-11 0.000

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000041 0.0000000019 0.0000000024 0.000

Elb/hr 4.59E-10 2.11E-10 2.66E-10 0.000

gr/dscf 1.99E-13 9.20E-14 1.13E-13 0.000

lb/mmBtuO2 9.33E-13 4.36E-13 5.55E-13 0.000

mg/dscm 4.55E-10 2.11E-10 2.59E-10 0.000

ng/dscm 4.55E-04 2.11E-04 2.59E-04 0.000

ng/dscm@7%O2 1.08E-03 5.07E-04 6.44E-04 0.001

ppm 2.57E-11 1.19E-11 1.46E-11 0.000

Compound: Other HpCDF

Average

RunNumber 2 3 1

Mass_mg 0.0000000022 0.0000000018 0.0000000043 0.000

Elb/hr 2.45E-10 1.99E-10 4.82E-10 0.000

Tuesday, February 22, 2011 Page 16 of 46
PSEG Sewaren Unit 1

9/30/2010

gr/dscf 1.07E-13 8.49E-14 2.09E-13 0.000

lb/mmBtuO2 5.05E-13 4.16E-13 9.79E-13 0.000

mg/dscm 2.44E-10 1.94E-10 4.78E-10 0.000

ng/dscm 2.44E-04 1.94E-04 4.78E-04 0.000

ng/dscm@7%O2 5.86E-04 4.82E-04 1.14E-03 0.001

ppm 1.43E-11 1.14E-11 2.81E-11 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000096 0.0000000066 0.000000007 0.000

Elb/hr 1.08E-09 7.34E-10 7.76E-10 0.000

gr/dscf 4.66E-13 3.20E-13 3.30E-13 0.000

lb/mmBtuO2 2.19E-12 1.52E-12 1.62E-12 0.000

mg/dscm 1.07E-09 7.32E-10 7.55E-10 0.000

ng/dscm 1.07E-03 7.32E-04 7.55E-04 0.001

ng/dscm@7%O2 2.54E-03 1.76E-03 1.88E-03 0.002

ppm 6.56E-11 4.50E-11 4.65E-11 0.000

Compound: Other HxCDF

Average

RunNumber 2 3 1

Mass_mg 0.0000000018 0.0000000016 0.0000000039 0.000

Elb/hr 2.00E-10 1.77E-10 4.37E-10 0.000

gr/dscf 8.72E-14 7.54E-14 1.89E-13 0.000

lb/mmBtuO2 4.13E-13 3.70E-13 8.88E-13 0.000

mg/dscm 2.00E-10 1.73E-10 4.33E-10 0.000

ng/dscm 2.00E-04 1.73E-04 4.33E-04 0.000

ng/dscm@7%O2 4.80E-04 4.30E-04 1.03E-03 0.001

ppm 1.28E-11 1.11E-11 2.78E-11 0.000

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000083 0.0000000029 0.0000000027 0.000

Elb/hr 9.29E-10 3.22E-10 2.99E-10 0.000

gr/dscf 4.03E-13 1.40E-13 1.27E-13 0.000

lb/mmBtuO2 1.89E-12 6.66E-13 6.25E-13 0.000

mg/dscm 9.22E-10 3.22E-10 2.91E-10 0.000

ng/dscm 9.22E-04 3.22E-04 2.91E-04 0.001

ng/dscm@7%O2 2.19E-03 7.73E-04 7.23E-04 0.001

ppm 6.22E-11 2.17E-11 1.97E-11 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000006 0.0000000019 0.0000000081 0.000

Elb/hr 6.72E-10 2.11E-10 8.98E-10 0.000

gr/dscf 2.91E-13 9.20E-14 3.82E-13 0.000

lb/mmBtuO2 1.37E-12 4.36E-13 1.87E-12 0.000

mg/dscm 6.66E-10 2.11E-10 8.74E-10 0.000

ng/dscm 6.66E-04 2.11E-04 8.74E-04 0.001

ng/dscm@7%O2 1.58E-03 5.07E-04 2.17E-03 0.001

ppm 4.71E-11 1.49E-11 6.17E-11 0.000

Tuesday, February 22, 2011 Page 17 of 46
PSEG Sewaren Unit 1

9/30/2010

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000045 0.0000000022 0.0000000027 0.000

Elb/hr 5.04E-10 2.45E-10 2.99E-10 0.000

gr/dscf 2.18E-13 1.07E-13 1.27E-13 0.000

lb/mmBtuO2 1.02E-12 5.05E-13 6.25E-13 0.000

mg/dscm 5.00E-10 2.44E-10 2.91E-10 0.000

ng/dscm 5.00E-04 2.44E-04 2.91E-04 0.000

ng/dscm@7%O2 1.19E-03 5.86E-04 7.23E-04 0.001

ppm 3.73E-11 1.82E-11 2.18E-11 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000055 0.0000000018 0.0000000044 0.000

Elb/hr 6.16E-10 2.00E-10 4.88E-10 0.000

gr/dscf 2.67E-13 8.72E-14 2.07E-13 0.000

lb/mmBtuO2 1.25E-12 4.13E-13 1.02E-12 0.000

mg/dscm 6.11E-10 2.00E-10 4.75E-10 0.000

ng/dscm 6.11E-04 2.00E-04 4.75E-04 0.000

ng/dscm@7%O2 1.45E-03 4.80E-04 1.18E-03 0.001

ppm 4.80E-11 1.57E-11 3.73E-11 0.000

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000000772 0.0000000373 0.0000000423 0.000

Elb/hr 8.65E-09 4.15E-09 4.69E-09 0.000

gr/dscf 3.75E-12 1.81E-12 1.99E-12 0.000

lb/mmBtuO2 1.76E-11 8.56E-12 9.79E-12 0.000

mg/dscm 8.57E-09 4.14E-09 4.56E-09 0.000

ng/dscm 8.57E-03 4.14E-03 4.56E-03 0.006

ng/dscm@7%O2 2.04E-02 9.94E-03 1.13E-02 0.014

ppm 0.000

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.0000000673 0.0000000277 0.0000000356 0.000

Elb/hr 7.54E-09 3.08E-09 3.95E-09 0.000

gr/dscf 3.27E-12 1.34E-12 1.68E-12 0.000

lb/mmBtuO2 1.53E-11 6.36E-12 8.24E-12 0.000

mg/dscm 7.47E-09 3.07E-09 3.84E-09 0.000

ng/dscm 7.47E-03 3.07E-03 3.84E-03 0.005

ng/dscm@7%O2 1.78E-02 7.37E-03 9.55E-03 0.012

ppm 0.000

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1-1 1-2 1-3

Elb/hr 3.02E-01 3.31E+04 7.67E-01 11,033.690

Tuesday, February 22, 2011 Page 18 of 46
PSEG Sewaren Unit 1

9/30/2010

gr/dscf 1.28E-04 1.39E-04 3.18E-04 0.000

lb/mmBtuO2 6.18E-04 6.83E-04 1.53E-03 0.001

mg/dscm 2.94E-01 3.19E-01 7.27E-01 0.447

ppm 1.60E-01 1.74E-01 3.97E-01 0.244

ppm@7%O2 3.90E-01 4.32E-01 9.68E-01 0.597

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 2 3 1

Mass_mg 1.8 3.5 0.94 2.080

Elb/hr 1.58E+00 2.97E+00 8.28E-01 1.793

lb/mmBtuO2 3.21E-03 6.22E-03 1.67E-03 0.004

mg/dscm 1.55E+00 3.01E+00 8.22E-01 1.794

mg/dscm@7%O2 3.71E+00 7.21E+00 1.94E+00 4.287

Compound: Hydrogen Fluoride

Average

RunNumber 2 3 1

Mass_mg 1.3 0.22 0.22 0.580

Elb/hr 1.14E+00 1.87E-01 1.94E-01 0.507

lb/mmBtuO2 2.32E-03 3.91E-04 3.91E-04 0.001

mg/dscm 1.12E+00 1.89E-01 1.92E-01 0.500

mg/dscm@7%O2 2.68E+00 4.53E-01 4.52E-01 1.195

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 3 1 2

Mass_mg 0.1912 0.1962 0.19425 0.194

Elb/hr 3.46E-02 3.56E-02 3.51E-02 0.035

lb/mmBtuO2 7.07E-05 7.29E-05 7.05E-05 0.000

mg/dscm 3.44E-02 3.51E-02 3.42E-02 0.035

mg/dscm@7%O2 8.20E-02 8.45E-02 8.18E-02 0.083

Compound: Arsenic

Average

RunNumber 3 1 2

Mass_mg 0.0053 0.0057 0.0053 0.005

Elb/hr 9.58E-04 1.03E-03 9.57E-04 0.001

lb/mmBtuO2 1.96E-06 2.12E-06 1.92E-06 0.000

mg/dscm 9.53E-04 1.02E-03 9.32E-04 0.001

mg/dscm@7%O2 2.27E-03 2.45E-03 2.23E-03 0.002

Compound: Beryllium

Average

RunNumber 3 1 2

Mass_mg 0.00153 0.00183 0.00183 0.002

Elb/hr 2.77E-04 3.32E-04 3.30E-04 0.000

lb/mmBtuO2 5.66E-07 6.80E-07 6.64E-07 0.000

mg/dscm 2.75E-04 3.27E-04 3.22E-04 0.000

mg/dscm@7%O2 6.56E-04 7.87E-04 7.70E-04 0.001

Tuesday, February 22, 2011 Page 19 of 46
PSEG Sewaren Unit 1

9/30/2010

Compound: Cadmium

Average

RunNumber 3 1 2

Mass_mg 0.00035 0.00035 0.00035 0.000

Elb/hr 6.33E-05 6.34E-05 6.32E-05 0.000

lb/mmBtuO2 1.29E-07 1.30E-07 1.27E-07 0.000

mg/dscm 6.29E-05 6.26E-05 6.15E-05 0.000

mg/dscm@7%O2 1.50E-04 1.51E-04 1.47E-04 0.000

Compound: Chromium

Average

RunNumber 3 1 2

Mass_mg 0.00553 0.00577 0.00466 0.005

Elb/hr 1.00E-03 1.05E-03 8.42E-04 0.001

lb/mmBtuO2 2.04E-06 2.14E-06 1.69E-06 0.000

mg/dscm 9.94E-04 1.03E-03 8.19E-04 0.001

mg/dscm@7%O2 2.37E-03 2.48E-03 1.96E-03 0.002

Compound: Cobalt

Average

RunNumber 3 1 2

Mass_mg 0.081375 0.086368 0.081875 0.083

Elb/hr 1.47E-02 1.57E-02 1.48E-02 0.015

lb/mmBtuO2 3.01E-05 3.21E-05 2.97E-05 0.000

mg/dscm 1.46E-02 1.55E-02 1.44E-02 0.015

mg/dscm@7%O2 3.48E-02 3.73E-02 3.45E-02 0.036

Compound: Filterable Particulate

Average

RunNumber 3 1 2

Mass_mg 20.6 19.4 21.5 20.500

Elb/hr 3.72E+00 3.52E+00 3.88E+00 3.707

lb/mmBtuO2 7.62E-03 7.21E-03 7.80E-03 0.008

mg/dscm 3.70E+00 3.47E+00 3.78E+00 3.650

mg/dscm@7%O2 8.82E+00 8.35E+00 9.04E+00 8.737

Compound: Lead

Average

RunNumber 3 1 2

Mass_mg 0.01579 0.01593 0.01577 0.016

Elb/hr 2.85E-03 2.89E-03 2.85E-03 0.003

lb/mmBtuO2 5.84E-06 5.92E-06 5.72E-06 0.000

mg/dscm 2.84E-03 2.85E-03 2.77E-03 0.003

mg/dscm@7%O2 6.77E-03 6.86E-03 6.63E-03 0.007

Compound: Manganese

Average

RunNumber 3 1 2

Mass_mg 0.1389 0.1403 0.1396 0.140

Elb/hr 2.51E-02 2.54E-02 2.52E-02 0.025

lb/mmBtuO2 5.14E-05 5.21E-05 5.07E-05 0.000

mg/dscm 2.50E-02 2.51E-02 2.45E-02 0.025

mg/dscm@7%O2 5.96E-02 6.04E-02 5.86E-02 0.060

Tuesday, February 22, 2011 Page 20 of 46
PSEG Sewaren Unit 1

9/30/2010

Compound: Nickel

Average

RunNumber 3 1 2

Mass_mg 1.4786 1.555 1.4559 1.497

Elb/hr 2.67E-01 2.82E-01 2.63E-01 0.271

lb/mmBtuO2 5.47E-04 5.78E-04 5.28E-04 0.001

mg/dscm 2.66E-01 2.78E-01 2.56E-01 0.267

mg/dscm@7%O2 6.34E-01 6.69E-01 6.13E-01 0.639

Compound: Selenium

Average

RunNumber 3 1 2

Mass_mg 0.0042 0.0035 0.0043 0.004

Elb/hr 7.59E-04 6.34E-04 7.77E-04 0.001

lb/mmBtuO2 1.55E-06 1.30E-06 1.56E-06 0.000

mg/dscm 7.55E-04 6.26E-04 7.56E-04 0.001

mg/dscm@7%O2 1.80E-03 1.51E-03 1.81E-03 0.002

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1-1 1-2 1-3

Elb/hr 1.19E+02 1.21E+02 1.22E+02 120.667

lb/mmBtuO2 2.64E-01 2.65E-01 2.64E-01 0.264

mg/dscm 1.26E+02 1.24E+02 1.26E+02 125.333

mg/dscm@7%O2 3.07E+02 3.08E+02 3.07E+02 307.333

ppm 4.72E+01 4.65E+01 4.71E+01 46.933

ppm@7%O2 1.15E+02 1.15E+02 1.15E+02 115.000

Location: Stack Exit - Method 6C 3

Compound: Sulfur Dioxide

Average

Run 3-1 3-2 3-3

Elb/hr 1.20E+02 1.16E+02 1.13E+02 116.333

lb/mmBtuO2 2.58E-01 2.60E-01 2.61E-01 0.260

mg/dscm 1.27E+02 1.26E+02 1.26E+02 126.333

mg/dscm@7%O2 2.99E+02 3.02E+02 3.02E+02 301.000

ppm 4.76E+01 4.72E+01 4.74E+01 47.400

ppm@7%O2 1.12E+02 1.13E+02 1.14E+02 113.000

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 3-1 3-2 3-3

Elb/hr 1.09E+02 1.21E+02 1.23E+02 117.667

lb/mmBtuO2 2.33E-01 2.55E-01 2.60E-01 0.249

mg/dscm 1.15E+02 1.24E+02 1.26E+02 121.667

mg/dscm@7%O2 2.71E+02 2.97E+02 3.02E+02 290.000

ppm 6.00E+01 6.46E+01 6.58E+01 63.467

ppm@7%O2 1.41E+02 1.55E+02 1.58E+02 151.333

Location: Stack Exit - OTM - 27/28

Tuesday, February 22, 2011 Page 21 of 46
PSEG Sewaren Unit 1

9/30/2010

Process Run Data

Compound: Filterable Particulate

Average

RunNumber 2 3 1

Mass_mg 16.9 18.6 14.5 16.667

Elb/hr 4.77E+00 5.20E+00 4.08E+00 4.683

gr/dscf 2.11E-03 2.24E-03 1.74E-03 0.002

lb/mmBtuO2 9.98E-03 1.05E-02 8.26E-03 0.010

mg/dscm 4.84E+00 5.13E+00 3.98E+00 4.650

ppm #Num!

Tuesday, February 22, 2011 Page 22 of 46
PSEG Sewaren Unit 1

9/30/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

2 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 

Run 1 M0011 

Start 7/15/2010 

8:20 End 

7/15/2010 10:35

0

2 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 1 M0011 

Start 7/15/2010 

8:20 End 

7/15/2010 10:35

0

2 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 1 M0011 

Start 7/15/2010 

8:20 End 

7/15/2010 10:35

0

3 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 

Runs 1-4 M0031 

Start 7/15/2010 

8:21 End 

7/15/2010 10:21

0

3 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Runs 1-4 M0031 

Start 7/15/2010 

8:21 End 

7/15/2010 10:21

0

3 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Runs 1-4 M0031 

Start 7/15/2010 

8:21 End 

7/15/2010 10:21

0

4 Fuel Oil Firing Rate 2601 gal/hr SEW1 Group 1 

Run 1 M18 (CH4) 

Start 7/15/2010 

17:38 End 

7/15/2010 17:42

0

4 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 1 M18 (CH4) 

Start 7/15/2010 

17:38 End 

7/15/2010 17:42

0

4 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 1 M18 (CH4) 

Start 7/15/2010 

17:38 End 

7/15/2010 17:42

0

Tuesday, February 22, 2011 Page 23 of 46
PSEG Sewaren Unit 1

9/30/2010

5 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 

Run 1 M6C (SO2) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

5 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 1 M6C (SO2) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

5 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 1 M6C (SO2) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

6 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 

Run 1 M10 (CO) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

6 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 1 M10 (CO) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

6 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 1 M10 (CO) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

7 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 

Run 1 M25A 

(TOC as propane) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

7 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 1 M25A 

(TOC as propane) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

7 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 1 M25A 

(TOC as propane) 

Start 7/15/2010 

8:21 End 

7/15/2010 10:26

0

Tuesday, February 22, 2011 Page 24 of 46
PSEG Sewaren Unit 1

9/30/2010

8 Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 1 

Run 2 M0010 

Start 7/15/2010 

11:01 End 

7/15/2010 13:15

0

8 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 2 M0010 

Start 7/15/2010 

11:01 End 

7/15/2010 13:15

0

8 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 2 M0010 

Start 7/15/2010 

11:01 End 

7/15/2010 13:15

0

9 Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 

Run 2 M10 (CO) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

9 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 2 M10 (CO) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

9 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 2 M10 (CO) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

10 Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 1 

Run 2 M0011 

Start 7/15/2010 

11:01 End 

7/15/2010 13:18

0

10 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 2 M0011 

Start 7/15/2010 

11:01 End 

7/15/2010 13:18

0

10 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 2 M0011 

Start 7/15/2010 

11:01 End 

7/15/2010 13:18

0

11 Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 1 

Runs 5-8 M0031 

Start 7/15/2010 

11:03 End 

7/15/2010 13:10

0

Tuesday, February 22, 2011 Page 25 of 46
PSEG Sewaren Unit 1

9/30/2010

11 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Runs 5-8 M0031 

Start 7/15/2010 

11:03 End 

7/15/2010 13:10

0

11 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Runs 5-8 M0031 

Start 7/15/2010 

11:03 End 

7/15/2010 13:10

0

12 Fuel Oil Firing Rate 2604 gal/hr SEW1 Group 1 

Run 2 M18 (CH4) 

Start 7/15/2010 

17:48 End 

7/15/2010 17:51

0

12 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 2 M18 (CH4) 

Start 7/15/2010 

17:48 End 

7/15/2010 17:51

0

12 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 2 M18 (CH4) 

Start 7/15/2010 

17:48 End 

7/15/2010 17:51

0

13 Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 

Run 2 M6C (SO2) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

13 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 2 M6C (SO2) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

13 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 2 M6C (SO2) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

14 Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 

Run 2 M25A 

(TOC as propane) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

Tuesday, February 22, 2011 Page 26 of 46
PSEG Sewaren Unit 1

9/30/2010

14 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 2 M25A 

(TOC as propane) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

14 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 2 M25A 

(TOC as propane) 

Start 7/15/2010 

11:02 End 

7/15/2010 13:01

0

15 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 

Run 3 M0010 

Start 7/15/2010 

13:55 End 

7/15/2010 16:18

0

15 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 3 M0010 

Start 7/15/2010 

13:55 End 

7/15/2010 16:18

0

15 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 3 M0010 

Start 7/15/2010 

13:55 End 

7/15/2010 16:18

0

16 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 

Run 3 M0011 

Start 7/15/2010 

13:55 End 

7/15/2010 16:17

0

16 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 3 M0011 

Start 7/15/2010 

13:55 End 

7/15/2010 16:17

0

16 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 3 M0011 

Start 7/15/2010 

13:55 End 

7/15/2010 16:17

0

17 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 

Runs 9-12 M0031 

Start 7/15/2010 

13:55 End 

7/15/2010 16:05

0

Tuesday, February 22, 2011 Page 27 of 46
PSEG Sewaren Unit 1

9/30/2010

17 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Runs 9-12 M0031 

Start 7/15/2010 

13:55 End 

7/15/2010 16:05

0

17 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Runs 9-12 M0031 

Start 7/15/2010 

13:55 End 

7/15/2010 16:05

0

18 Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 

Run 3 M18 (CH4) 

Start 7/15/2010 

17:57 End 

7/15/2010 18:00

0

18 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 3 M18 (CH4) 

Start 7/15/2010 

17:57 End 

7/15/2010 18:00

0

18 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 3 M18 (CH4) 

Start 7/15/2010 

17:57 End 

7/15/2010 18:00

0

19 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 

Run 3 M6C (SO2) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

19 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 3 M6C (SO2) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

19 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 3 M6C (SO2) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

20 Fuel Oil Firing Rate 2595 gal/hr SEW1 Group 2 

Run 1 M23 Start 

7/13/2010 20:00 

End 7/14/2010 

4:15

0

20 Unit Gross Electrical Output 32 Mwe SEW1 Group 2 

Run 1 M23 Start 

7/13/2010 20:00 

End 7/14/2010 

4:15

0

Tuesday, February 22, 2011 Page 28 of 46
PSEG Sewaren Unit 1

9/30/2010

20 Unit Net Electric Generation 30 MWh SEW1 Group 2 

Run 1 M23 Start 

7/13/2010 20:00 

End 7/14/2010 

4:15

0

21 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 

Run 3 M10 (CO) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

21 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 3 M10 (CO) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

21 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 3 M10 (CO) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

22 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 

Run 3 M25A 

(TOC as propane) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

22 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 

Run 3 M25A 

(TOC as propane) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

22 Unit Net Electric Generation 31 MWh SEW1 Group 1 

Run 3 M25A 

(TOC as propane) 

Start 7/15/2010 

13:56 End 

7/15/2010 15:55

0

23 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 2 

Run 2 M23 Start 

7/14/2010 21:35 

End 7/15/2010 

5:52

0

23 Unit Gross Electrical Output 32 Mwe SEW1 Group 2 

Run 2 M23 Start 

7/14/2010 21:35 

End 7/15/2010 

5:52

0

Tuesday, February 22, 2011 Page 29 of 46
PSEG Sewaren Unit 1

9/30/2010

23 Unit Net Electric Generation 30 MWh SEW1 Group 2 

Run 2 M23 Start 

7/14/2010 21:35 

End 7/15/2010 

5:52

0

24 Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 2 

Run 3 M23 Start 

7/15/2010 20:08 

End 7/16/2010 

4:24

0

24 Unit Gross Electrical Output 32 Mwe SEW1 Group 2 

Run 3 M23 Start 

7/15/2010 20:08 

End 7/16/2010 

4:24

0

24 Unit Net Electric Generation 30 MWh SEW1 Group 2 

Run 3 M23 Start 

7/15/2010 20:08 

End 7/16/2010 

4:24

0

25 Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 3 

Run 1 M26A Start 

7/13/2010 17:16 

End 7/13/2010 

18:27

0

25 Unit Gross Electrical Output 32 Mwe SEW1 Group 3 

Run 1 M26A Start 

7/13/2010 17:16 

End 7/13/2010 

18:27

0

25 Unit Net Electric Generation 30 MWh SEW1 Group 3 

Run 1 M26A Start 

7/13/2010 17:16 

End 7/13/2010 

18:27

0

26 Fuel Oil Firing Rate 2608 gal/hr SEW1 Group 3 

Run 1 M6C (SO2) 

Start 7/15/2010 

17:18 End 

7/15/2010 18:24

0

26 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 1 M6C (SO2) 

Start 7/15/2010 

17:18 End 

7/15/2010 18:24

0

26 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 1 M6C (SO2) 

Start 7/15/2010 

17:18 End 

7/15/2010 18:24

0

Tuesday, February 22, 2011 Page 30 of 46
PSEG Sewaren Unit 1

9/30/2010

27 Fuel Oil Firing Rate 2608 gal/hr SEW1 Group 3 

Run 1 M7E (NOx) 

Start 7/15/2010 

17:18 End 

7/15/2010 18:24

0

27 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 1 M7E (NOx) 

Start 7/15/2010 

17:18 End 

7/15/2010 18:24

0

27 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 1 M7E (NOx) 

Start 7/15/2010 

17:18 End 

7/15/2010 18:24

0

28 Fuel Oil Firing Rate 2609 gal/hr SEW1 Group 3 

Run 2 M26A Start 

7/15/2010 17:03 

End 7/15/2010 

18:12

0

28 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 2 M26A Start 

7/15/2010 17:03 

End 7/15/2010 

18:12

0

28 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 2 M26A Start 

7/15/2010 17:03 

End 7/15/2010 

18:12

0

29 Fuel Oil Firing Rate 2610 gal/hr SEW1 Group 3 

Run 2 M6C (SO2) 

Start 7/15/2010 

17:04 End 

7/15/2010 18:03

0

29 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 2 M6C (SO2) 

Start 7/15/2010 

17:04 End 

7/15/2010 18:03

0

29 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 2 M6C (SO2) 

Start 7/15/2010 

17:04 End 

7/15/2010 18:03

0

30 Fuel Oil Firing Rate 2610 gal/hr SEW1 Group 3 

Run 2 M7E (NOx) 

Start 7/15/2010 

17:04 End 

7/15/2010 18:03

0

Tuesday, February 22, 2011 Page 31 of 46
PSEG Sewaren Unit 1

9/30/2010

30 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 2 M7E (NOx) 

Start 7/15/2010 

17:04 End 

7/15/2010 18:03

0

30 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 2 M7E (NOx) 

Start 7/15/2010 

17:04 End 

7/15/2010 18:03

0

31 Fuel Oil Firing Rate 2612 gal/hr SEW1 Group 3 

Run 3 M26A Start 

7/15/2010 18:23 

End 7/15/2010 

19:32

0

31 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 3 M26A Start 

7/15/2010 18:23 

End 7/15/2010 

19:32

0

31 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 3 M26A Start 

7/15/2010 18:23 

End 7/15/2010 

19:32

0

32 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 3 

Run 3 M6C (SO2) 

Start 7/15/2010 

18:23 End 

7/15/2010 19:22

0

32 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 3 M6C (SO2) 

Start 7/15/2010 

18:23 End 

7/15/2010 19:22

0

32 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 3 M6C (SO2) 

Start 7/15/2010 

18:23 End 

7/15/2010 19:22

0

33 Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 3 

Run 3 M7E (NOx) 

Start 7/15/2010 

18:23 End 

7/15/2010 19:22

0

33 Unit Gross Electrical Output 33 Mwe SEW1 Group 3 

Run 3 M7E (NOx) 

Start 7/15/2010 

18:23 End 

7/15/2010 19:22

0

Tuesday, February 22, 2011 Page 32 of 46
PSEG Sewaren Unit 1

9/30/2010

33 Unit Net Electric Generation 31 MWh SEW1 Group 3 

Run 3 M7E (NOx) 

Start 7/15/2010 

18:23 End 

7/15/2010 19:22

0

34 Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 4 

Run 2 M29 Start 

7/14/2010 7:37 

End 7/14/2010 

12:52

0

34 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 2 M29 Start 

7/14/2010 7:37 

End 7/14/2010 

12:52

0

34 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 2 M29 Start 

7/14/2010 7:37 

End 7/14/2010 

12:52

0

35 Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 4 

Run 2 

OTM027/028 Start 

7/14/2010 7:37 

End 7/14/2010 

13:21

0

35 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 2 

OTM027/028 Start 

7/14/2010 7:37 

End 7/14/2010 

13:21

0

35 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 2 

OTM027/028 Start 

7/14/2010 7:37 

End 7/14/2010 

13:21

0

36 Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 4 

Run 2 M30B Start 

7/14/2010 7:37 

End 7/14/2010 

13:37

0

36 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 2 M30B Start 

7/14/2010 7:37 

End 7/14/2010 

13:37

0

Tuesday, February 22, 2011 Page 33 of 46
PSEG Sewaren Unit 1

9/30/2010

36 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 2 M30B Start 

7/14/2010 7:37 

End 7/14/2010 

13:37

0

37 Fuel Oil Firing Rate 2590 gal/hr SEW1 Group 4 

Run 3 M29 Start 

7/14/2010 14:50 

End 7/14/2010 

20:11

0

37 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 3 M29 Start 

7/14/2010 14:50 

End 7/14/2010 

20:11

0

37 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 3 M29 Start 

7/14/2010 14:50 

End 7/14/2010 

20:11

0

38 Fuel Oil Firing Rate 2590 gal/hr SEW1 Group 4 

Run 3 

OTM027/028 Start 

7/14/2010 14:50 

End 7/14/2010 

20:37

0

38 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 3 

OTM027/028 Start 

7/14/2010 14:50 

End 7/14/2010 

20:37

0

38 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 3 

OTM027/028 Start 

7/14/2010 14:50 

End 7/14/2010 

20:37

0

39 Fuel Oil Firing Rate 2590 gal/hr SEW1 Group 4 

Run 3 M30B Start 

7/14/2010 14:31 

End 7/14/2010 

20:31

0

39 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 3 M30B Start 

7/14/2010 14:31 

End 7/14/2010 

20:31

0

Tuesday, February 22, 2011 Page 34 of 46
PSEG Sewaren Unit 1

9/30/2010

39 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 3 M30B Start 

7/14/2010 14:31 

End 7/14/2010 

20:31

0

40 Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 4 

Run 1 M29 Start 

7/13/2010 10:39 

End 7/13/2010 

15:59

0

40 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 1 M29 Start 

7/13/2010 10:39 

End 7/13/2010 

15:59

0

40 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 1 M29 Start 

7/13/2010 10:39 

End 7/13/2010 

15:59

0

41 Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 4 

Run 1 

OTM027/028 Start 

7/13/2010 10:39 

End 7/13/2010 

16:40

0

41 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 1 

OTM027/028 Start 

7/13/2010 10:39 

End 7/13/2010 

16:40

0

41 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 1 

OTM027/028 Start 

7/13/2010 10:39 

End 7/13/2010 

16:40

0

42 Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 4 

Run 1 M30B Start 

7/13/2010 10:41 

End 7/13/2010 

16:41

0

42 Unit Gross Electrical Output 32 Mwe SEW1 Group 4 

Run 1 M30B Start 

7/13/2010 10:41 

End 7/13/2010 

16:41

0

Tuesday, February 22, 2011 Page 35 of 46
PSEG Sewaren Unit 1

9/30/2010

APCD Run Data

Process Lab Run Data

42 Unit Net Electric Generation 30 MWh SEW1 Group 4 

Run 1 M30B Start 

7/13/2010 10:41 

End 7/13/2010 

16:41

0

1 Heat Input Million Btus/million BTU using O2 0 0

1 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 

Run 1 M0010 

Start 7/15/2010 

8:20 End 

7/15/2010 10:36

0

1 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 

Run 1 M0010 

Start 7/15/2010 

8:20 End 

7/15/2010 10:36

0

1 Unit Net Electric Generation 30 MWh SEW1 Group 1 

Run 1 M0010 

Start 7/15/2010 

8:20 End 

7/15/2010 10:36

0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

1 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

1 Fuel Nickel Content 0 ppm

1 Fuel Arsenic Content 0 ppm

1 Fuel Chromium Content 0 ppm

1 Fuel Beryllium Content 0 ppm

1 Fuel Lead Content 0 ppm

1 Fuel Manganese Content 0 ppm

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Tuesday, February 22, 2011 Page 36 of 46
PSEG Sewaren Unit 1

9/30/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:20:00 AM 11:01:00 AM 1:55:00 PM

Run Finish Time 10:35:00 AM 1:18:00 PM 4:17:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.286 0.286 0.286 0.286

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988

Barometric Pressure, inches of Mercury 29.745 29.68 29.715 29.713

Average Orifice Meter Differential, inches H2O 1.67 1.71 1.76 1.713

Dry Gas Meter Volume Sampled, cubic feet 85.685 88.199 90.044 87.976

Average Dry Gas Meter Temperature, °F 87.88 94.83 96.67 93.127

Dry Gas Meter Volume Sampled, dscf 81.459 82.627 84.185 82.757

Total Moisture Liquid collected, g 104.2 104.6 105.3 104.700

Volume of Water Vapor, standard cubic feet 4.90 4.92 4.96 4.927

Moisture Content of Stack Gas, % 5.67 5.62 5.56 5.617

Moisture Saturation at Stack Gas Temperature, % 87.05 90.10 96.11 91.087

Dry Mole Fraction 0.9433 0.9438 0.9444 0.944

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Carbon Monoxide & Nitrogen, % 80.5 80.5 80.5 80.500

Fuel Factor 1.33 1.33 1.33

Dry Molecular Weight, lb/lb-Mole 29.30 29.28 29.30 29.293

Wet Molecular weight, lb/lb-Mole 28.66 28.65 28.67 28.660

Flue Gas Static Pressure, inches of H2O -0.29 -0.29 -0.29 -0.290

Absolute Flue Gas Pressure, inches of Mercury 29.72 29.66 29.69 29.690

Average Stack Gas Temperature, °F 204.79 206.38 209.63 206.933

Average Velocity Head, inches of H2O 0.3137310707

43151

0.321087307

300618

0.333166737

610149

0.323

Average Stack Gas Velocity, feet/second 35.53 36.03 36.76 36.107

Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703

Dry Volumetric Flow Rate, dry scfm 273,988.8 276,768.6 281,468.8 277,408.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 368,168.3 373,349.3 380,913.7 374,143.767

Percent Isokinetic of Sampling Rate, % 95.9 96.3 96.5 96.233

Percent Excess Air, % 251.2 257.1 251.2 253.167

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.833 14.833 14.833

Rectangular Duct Width, inches 157.7 157.7 157.7

Rectangular Duct Length, inches 157.7 157.7 157.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 37 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 10

Average

Run Number 1-1 1-2 1-3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:21:00 AM 11:02:00 AM 1:56:00 PM

Run Finish Time 10:26:00 AM 1:01:00 PM 3:55:00 PM

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Fuel Factor 1.33 1.33 0

Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4 258,298.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Analyzer Make Thermo 

Scientific

Thermo 

Scientific

Thermo 

Scientific

Analyzer Model 48i 48i 48i

Analyzer Serial Number CMO8460052 CMO846005

2

CMO846005

2

Operating Range 99.5 99.5 99.5 99.500

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 11 11 11 11.000

Calibration Pre Zero Cylinder ID Nitrogen-CO Nitrogen-CO Nitrogen-CO

Calibration Pre Zero Cylinder Instrument Response 0.317 0.317 0.073 0.236

Calibration Pre Zero Cylinder Bias 0.06 0.1 -0.02 0.047

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID BBB00000-

CO-Mid

BBB00000-

CO-Mid

BBB00000-

CO-Mid

Calibration Pre High Cylinder Instrument Response 50.39 50.805 49.658 50.284

Calibration Pre High Cylinder Bias -0.12 0.09 -0.49 -0.173

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-CO Nitrogen-CO Nitrogen-CO

Calibration Post Zero Cylinder Instrument Response 0.317 0.073 0.048 0.146

Calibration Post Zero Cylinder Bias 0.06 -0.02 -0.04 0.000

Calibration Post Zero Cylinder Drift 0 0.12 0.02 0.047

Calibration Post High Cylinder ID BBB00000-

CO-Mid

BBB00000-

CO-Mid

BBB00000-

CO-Mid

Calibration Post High Cylinder Instrument Response 50.805 49.658 49.755 50.073

Calibration Post High Cylinder Bias 0.09 -0.49 -0.44 -0.280

Calibration Post High Cylinder Drift 0.21 0.58 0.05 0.280

Cavg -0.353 -0.503 -0.528 -0.461

Cavg Units ppmvd ppmvd ppmvd

Cgas 0 0 0 0.000

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 38 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 7/13/2010 7/14/2010 7/15/2010

Run Start Time 4:15:00 AM 5:52:00 AM 4:24:00 AM

Run Finish Time 8:00:00 PM 9:35:00 PM 8:08:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.283 0.283 0.286 0.284

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9971 0.9971 0.9971 0.997

Barometric Pressure, inches of Mercury 29.74 29.825 29.88 29.815

Average Orifice Meter Differential, inches H2O 1.68 1.65 1.80 1.710

Dry Gas Meter Volume Sampled, cubic feet 333.467 327.276 339.742 333.495

Average Dry Gas Meter Temperature, °F 90.98 81.35 88.15 86.827

Dry Gas Meter Volume Sampled, dscf 318.031 318.560 327.311 321.301

Total Moisture Liquid collected, g 429.7 411.4 419.2 420.100

Volume of Water Vapor, standard cubic feet 20.23 19.36 19.73 19.773

Moisture Content of Stack Gas, % 5.98 5.73 5.69 5.800

Moisture Saturation at Stack Gas Temperature, % 81.90 84.08 84.71 83.563

Dry Mole Fraction 0.9402 0.9427 0.9431 0.942

Carbon Dioxide, % 4.368 4.3 4.164 4.277

Oxygen, % 15.051 15.111 15.308 15.157

Carbon Monoxide & Nitrogen, % 80.581 80.589 80.528 80.566

Fuel Factor 1.34 1.35 1.34

Dry Molecular Weight, lb/lb-Mole 29.30 29.29 29.28 29.290

Wet Molecular weight, lb/lb-Mole 28.62 28.64 28.64 28.633

Flue Gas Static Pressure, inches of H2O 0.26 0.25 0.255 0.255

Absolute Flue Gas Pressure, inches of Mercury 29.76 29.84 29.90 29.833

Average Stack Gas Temperature, °F 201.88 203.29 203.75 202.973

Average Velocity Head, inches of H2O 0.3027931239

86649

0.297985888

672368

0.311735218

519044

0.304

Average Stack Gas Velocity, feet/second 34.83 34.53 35.30 34.887

Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703

Dry Volumetric Flow Rate, dry scfm 269,247.0 267,786.6 274,234.8 270,422.800

Actual Wet Volumetric Flue Gas Flow Rate, acfm 360,914.7 357,806.1 365,785.0 361,501.933

Percent Isokinetic of Sampling Rate, % 97.3 98.0 96.3 97.200

Percent Excess Air, % 241.9 245.1 257.2 248.067

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.833 14.833 14.833

Rectangular Duct Width, inches 157.7 157.7 157.7

Rectangular Duct Length, inches 157.7 157.7 157.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 39 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 25A

Average

Run Number 1-1 1-2 1-3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:21:00 AM 11:02:00 AM 1:56:00 PM

Run Finish Time 10:26:00 AM 1:01:00 PM 3:55:00 PM

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Fuel Factor 1.33 1.33 1.33

Dry Volumetric Flow Rate, dry scfm 273988.8 2767686000

0

281468.8 9,225,805,1

52.533

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 51C 51C 51C

Analyzer Serial Number 0327202203 0327202203 0327202203 327,202,203

.000

Operating Range 10 10 10 10.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 911 911 911 911.000

Calibration Pre Zero Cylinder ID Nitrogen-THC NitrogenTHCNitrogenTHC

Calibration Pre Zero Cylinder Instrument Response 0.092 0.102 0.012 0.069

Calibration Pre Zero Cylinder Bias 0.4 0.5 -0.4 0.167

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CCC00000-

THC-Low

CCC00000-

THC-Low

CCC00000-

THC-Low

Calibration Pre High Cylinder Instrument Response 3.322 3.234 3.19 3.249

Calibration Pre High Cylinder Bias 2.12 1.24 0.8 1.387

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-THC NitrogenTHCNitrogenTHC

Calibration Post Zero Cylinder Instrument Response 0.102 0.012 0.021 0.045

Calibration Post Zero Cylinder Bias 0.5 -0.4 -0.31 -0.070

Calibration Post Zero Cylinder Drift 0.1 0.9 0.09 0.363

Calibration Post High Cylinder ID CCC00000-

THC-Low

CCC00000-

THC-Low

CCC00000-

THC-Low

Calibration Post High Cylinder Instrument Response 3.234 3.19 3.281 3.235

Calibration Post High Cylinder Bias 1.24 0.8 1.71 1.250

Calibration Post High Cylinder Drift 0.88 0.44 0.91 0.743

Cavg 0.267 0.24 0.442 0.316

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.1603 0.174 0.3966 0.244

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 40 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 7/13/2010 7/15/2010 7/15/2010

Run Start Time 5:16:00 PM 5:03:00 PM 6:23:00 PM

Run Finish Time 6:27:00 PM 6:12:00 PM 7:32:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.283 0.286 0.286 0.285

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9971 0.9971 0.9971 0.997

Barometric Pressure, inches of Mercury 29.73 29.875 29.87 29.825

Average Orifice Meter Differential, inches H2O 1.77 1.80 1.83 1.800

Dry Gas Meter Volume Sampled, cubic feet 42.567 42.918 43.290 42.925

Average Dry Gas Meter Temperature, °F 93.71 93.56 96.29 94.520

Dry Gas Meter Volume Sampled, dscf 40.392 40.937 41.085 40.805

Total Moisture Liquid collected, g 81.9 60.6 103.9 82.133

Volume of Water Vapor, standard cubic feet 3.86 2.85 4.89 3.867

Moisture Content of Stack Gas, % 8.72 6.51 10.64 8.623

Moisture Saturation at Stack Gas Temperature, % 85.48 89.36 88.01 87.617

Dry Mole Fraction 0.9128 0.9349 0.8936 0.914

Carbon Dioxide, % 4.4 4.3 4.3 4.333

Oxygen, % 15 15.1 15.1 15.067

Carbon Monoxide & Nitrogen, % 80.6 80.6 80.6 80.600

Fuel Factor 1.34 1.35 1.35

Dry Molecular Weight, lb/lb-Mole 29.30 29.29 29.29 29.293

Wet Molecular weight, lb/lb-Mole 28.31 28.56 28.09 28.320

Flue Gas Static Pressure, inches of H2O -0.29 -0.29 -0.29 -0.290

Absolute Flue Gas Pressure, inches of Mercury 29.71 29.85 29.85 29.803

Average Stack Gas Temperature, °F 203.88 206.29 205.54 205.237

Average Velocity Head, inches of H2O 0.3187229638

03731

0.311207403

471707

0.315416515

150918

0.315

Average Stack Gas Velocity, feet/second 36.02 35.42 35.93 35.790

Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703

Dry Volumetric Flow Rate, dry scfm 269,064.2 271,280.3 263,326.2 267,890.233

Actual Wet Volumetric Flue Gas Flow Rate, acfm 373,245.7 367,028.4 372,313.1 370,862.400

Percent Isokinetic of Sampling Rate, % 98.9 97.4 100.7 99.000

Percent Excess Air, % 238.9 244.4 244.4 242.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.833 14.833 14.833

Rectangular Duct Width, inches 157.7 157.7 157.7

Rectangular Duct Length, inches 157.7 157.7 157.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 41 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 7/13/2010 7/14/2010 7/14/2010

Run Start Time 10:39:00 AM 7:37:00 AM 2:50:00 PM

Run Finish Time 3:59:00 PM 12:52:00 PM 8:11:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 300 300 300

Nozzle Diameter, inches 0.283 0.283 0.283 0.283

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9971 0.9971 0.9971 0.997

Barometric Pressure, inches of Mercury 29.58 29.77 29.795 29.715

Average Orifice Meter Differential, inches H2O 1.70 1.73 1.65 1.693

Dry Gas Meter Volume Sampled, cubic feet 206.819 209.429 201.832 206.027

Average Dry Gas Meter Temperature, °F 87.73 88.50 80.73 85.653

Dry Gas Meter Volume Sampled, dscf 197.362 200.864 196.485 198.237

Total Moisture Liquid collected, g 297.9 283.1 264.4 281.800

Volume of Water Vapor, standard cubic feet 14.02 13.33 12.45 13.267

Moisture Content of Stack Gas, % 6.63 6.22 5.96 6.270

Moisture Saturation at Stack Gas Temperature, % 78.30 83.27 80.75 80.773

Dry Mole Fraction 0.9337 0.9378 0.9404 0.937

Carbon Dioxide, % 4.341 4.339 4.315 4.332

Oxygen, % 15.124 15.091 15.072 15.096

Carbon Monoxide & Nitrogen, % 80.535 80.57 80.613 80.573

Fuel Factor 1.33 1.34 1.35

Dry Molecular Weight, lb/lb-Mole 29.30 29.30 29.29 29.297

Wet Molecular weight, lb/lb-Mole 28.55 28.60 28.62 28.590

Flue Gas Static Pressure, inches of H2O -0.29 -0.29 -0.29 -0.290

Absolute Flue Gas Pressure, inches of Mercury 29.56 29.75 29.77 29.693

Average Stack Gas Temperature, °F 199.38 202.67 201.21 201.087

Average Velocity Head, inches of H2O 0.3097998203

23559

0.315852208

530573

0.300525792

208104

0.309

Average Stack Gas Velocity, feet/second 35.33 35.62 34.68 35.210

Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703

Dry Volumetric Flow Rate, dry scfm 270,422.7 274,231.5 268,506.4 271,053.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 366,095.8 369,100.9 359,360.4 364,852.367

Percent Isokinetic of Sampling Rate, % 96.2 96.5 96.4 96.367

Percent Excess Air, % 246.4 244.2 242.7 244.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.833 14.833 14.833

Rectangular Duct Width, inches 157.7 157.7 157.7

Rectangular Duct Length, inches 157.7 157.7 157.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 42 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 6C

Average

Run Number 1-1 1-2 1-3

Test Date 7/15/2010 7/15/2010 7/15/2010

Run Start Time 8:21:00 AM 11:02:00 AM 1:56:00 PM

Run Finish Time 10:26:00 AM 1:01:00 PM 3:55:00 PM

Carbon Dioxide, % 4.3 4.2 4.3 4.267

Oxygen, % 15.2 15.3 15.2 15.233

Fuel Factor 1.33 1.33 1.33

Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4 258,298.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Analyzer Make Ametek Ametek Ametek

Analyzer Model 921CD 921CD 921CD

Analyzer Serial Number AE-921-6434 AE-921-

6434

AE-921-6434

Operating Range 201 201 201 201.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 411 411 411 411.000

Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Pre Zero Cylinder Instrument Response 2.355 4.416 3.729 3.500

Calibration Pre Zero Cylinder Bias 0.27 1.29 0.95 0.837

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID AAL21250-

SO2-Mid

AAL21250-

SO2-Mid

AAL21250-

SO2-Mid

Calibration Pre High Cylinder Instrument Response 108.351 107.321 106.535 107.402

Calibration Pre High Cylinder Bias -1.07 -1.59 -1.98 -1.547

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Post Zero Cylinder Instrument Response 4.416 3.729 3.238 3.794

Calibration Post Zero Cylinder Bias 1.29 0.95 0.71 0.983

Calibration Post Zero Cylinder Drift 1.02 0.34 0.24 0.533

Calibration Post High Cylinder ID AAL21250-

SO2-Mid

AAL21250-

SO2-Mid

AAL21250-

SO2-Mid

Calibration Post High Cylinder Instrument Response 107.321 106.535 106.634 106.830

Calibration Post High Cylinder Bias -1.59 -1.98 -1.93 -1.833

Calibration Post High Cylinder Drift 0.52 0.39 0.05 0.320

Cavg 48.495 47.872 47.986 48.118

Cavg Units ppmvd ppmvd ppmvd

Cgas 47.1607 46.5012 47.1351 46.932

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 43 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 6C 3

Average

Run Number 3-1 3-2 3-3

Test Date 7/13/2010 7/15/2010 7/15/2010

Run Start Time 5:18:00 PM 5:04:00 PM 6:23:00 PM

Run Finish Time 6:24:00 PM 6:03:00 PM 7:22:00 PM

Carbon Dioxide, % 4.4 4.3 4.3 4.333

Oxygen, % 15 15.1 15.1 15.067

Fuel Factor 0 1.35 1.35

Dry Volumetric Flow Rate, dry scfm 252456.3 245857.5 238787.9 245,700.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 4.83 6.51 10.64 7.327

Analyzer Make Ametek Ametek Ametek

Analyzer Model 921CE 921CE 921CE

Analyzer Serial Number AE-921-6434 AD-921-

6434

AE-921-6434

Operating Range 201 201 201 201.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 611 412 412 478.333

Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Pre Zero Cylinder Instrument Response 1.995 3.238 2.935 2.723

Calibration Pre Zero Cylinder Bias 0 0.71 0.56 0.423

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM045659-

SO2-Mid

AAL21250-

SO2-Mid

AAL21250-

SO2-Mid

Calibration Pre High Cylinder Instrument Response 97.332 106.634 106.32 103.429

Calibration Pre High Cylinder Bias -2.07 -1.93 -2.08 -2.027

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Post Zero Cylinder Instrument Response 2.888 2.935 3.238 3.020

Calibration Post Zero Cylinder Bias 0.45 0.56 0.71 0.573

Calibration Post Zero Cylinder Drift 0.45 0.15 0.15 0.250

Calibration Post High Cylinder ID ALM045659-

SO2-Mid

AAL21250-

SO2-Mid

AAL21250-

SO2-Mid

Calibration Post High Cylinder Instrument Response 96.969 106.32 106.634 103.308

Calibration Post High Cylinder Bias -2.25 -2.08 -1.93 -2.087

Calibration Post High Cylinder Drift 0.18 0.15 0.15 0.160

Cavg 47.958 47.773 47.943 47.891

Cavg Units ppmvd ppmvd ppmvd

Cgas 47.5787 47.1974 47.377 47.384

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 44 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - Method 7E

Average

Run Number 3-1 3-2 3-3

Test Date 7/13/2010 7/15/2010 7/15/2010

Run Start Time 5:18:00 PM 5:04:00 PM 6:23:00 PM

Run Finish Time 6:24:00 PM 6:03:00 PM 7:22:00 PM

Carbon Dioxide, % 4.4 4.3 4.3 4.333

Oxygen, % 15 15.1 15.1 15.067

Fuel Factor 1.34 1.35 1.35

Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4 258,298.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.67 3.48 5.56 4.903

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 42CLS 42CLS 42CLS

Analyzer Serial Number 0328202427 0328202427 0328202427 328,202,427

.000

Operating Range 201 201 201 201.000

Operating Units ppm PPM ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 112 111 111 111.333

Calibration Pre Zero Cylinder ID Nitrogen-NOx NitrogenNOxNitrogenNOx

Calibration Pre Zero Cylinder Instrument Response 0.322 0.329 0.422 0.358

Calibration Pre Zero Cylinder Bias 0.21 0 0.04 0.083

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM045659-

NOx-Mid

AAL21250-

NOx-Mid

AAL21250-

NOx-Mid

Calibration Pre High Cylinder Instrument Response 100.2 107.835 107.911 105.315

Calibration Pre High Cylinder Bias -0.93 -0.84 -0.8 -0.857

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-NOx NitrogenNOxNitrogenNOx

Calibration Post Zero Cylinder Instrument Response 0.392 0.422 0.411 0.408

Calibration Post Zero Cylinder Bias 0.24 0.04 0.25 0.177

Calibration Post Zero Cylinder Drift 0.03 0.04 1.9 0.657

Calibration Post High Cylinder ID ALM045659-

NOx-Mid

AAL21250-

NOx-Mid

AAL21250-

NOx-Mid

Calibration Post High Cylinder Instrument Response 99.42 107.911 106.333 104.555

Calibration Post High Cylinder Bias -1.32 -0.8 -1.59 -1.237

Calibration Post High Cylinder Drift 0.39 3.999999999

99999E-02

0.79 0.407

Cavg 60.528 63.039 63.761 62.443

Cavg Units ppmvd ppmvd ppmvd

Cgas 60.0179 64.5886 65.7752 63.461

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 45 of 46
PSEG Sewaren Unit 1

9/30/2010

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 7/13/2010 7/14/2010 7/14/2010

Run Start Time 10:39:00 AM 7:37:00 AM 2:50:00 PM

Run Finish Time 4:40:00 PM 1:21:00 PM 8:37:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 335.42 330.1 330.63

Nozzle Diameter, inches 0.207 0.207 0.207 0.207

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988

Barometric Pressure, inches of Mercury 29.575 29.77 29.78 29.708

Average Orifice Meter Differential, inches H2O 0.45 0.45 0.45 0.450

Dry Gas Meter Volume Sampled, cubic feet 136.658 130.761 134.692 134.037

Average Dry Gas Meter Temperature, °F 88.58 90.75 86.58 88.637

Dry Gas Meter Volume Sampled, dscf 128.624 123.396 128.119 126.713

Total Moisture Liquid collected, g 188.8 168.2 176 177.667

Volume of Water Vapor, standard cubic feet 8.89 7.92 8.28 8.363

Moisture Content of Stack Gas, % 6.46 6.03 6.07 6.187

Moisture Saturation at Stack Gas Temperature, % 96.80 94.08 100.00 96.960

Dry Mole Fraction 0.9354 0.9397 0.9393 0.938

Carbon Dioxide, % 4.341 4.339 4.315 4.332

Oxygen, % 15.124 15.091 15.072 15.096

Carbon Monoxide & Nitrogen, % 80.535 80.57 80.613 80.573

Fuel Factor 1.33 1.34 1.35

Dry Molecular Weight, lb/lb-Mole 29.30 29.30 29.29 29.297

Wet Molecular weight, lb/lb-Mole 28.57 28.62 28.60 28.597

Flue Gas Static Pressure, inches of H2O -0.29 -0.29 0.29 -0.097

Absolute Flue Gas Pressure, inches of Mercury 29.55 29.75 29.80 29.700

Average Stack Gas Temperature, °F 209.75 208.67 214.25 210.890

Average Velocity Head, inches of H2O 0.3210645728

28574

0.293201106

633757

0.311593043

91876

0.309

Average Stack Gas Velocity, feet/second 36.24 34.46 35.65 35.450

Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703

Dry Volumetric Flow Rate, dry scfm 273,497.8 263,453.0 270,634.2 269,195.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 375,525.4 357,080.7 369,411.7 367,339.267

Percent Isokinetic of Sampling Rate, % 103.6 104.9 105.8 104.767

Percent Excess Air, % 246.4 244.2 242.7 244.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.833 14.833 14.833

Rectangular Duct Width, inches 157.7 157.7 157.7

Rectangular Duct Length, inches 157.7 157.7 157.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 46 of 46