### Name: Lois A. Knowlson

Title: Senior Environmental Engineer Company: PSEG Fossil Sign Date: 9/30/2010 Name: Anthony Fortunato Title: Senior Testing Supervisor Company:PSEG Maplewood Testing Services Sign Date: 9/30/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## PSEG Sewaren Unit 1 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Tuesday, February 22, 2011 Page 1 of 46

### PSEG Sewaren Unit 1
9/30/2010 Facility Information: PSEG Sewaren Generating Station
751 Cliff Road

Sewaren NJ07077 Contact:Joseph D. Krejsa Phone: Fax: Email:joseph.krejsa@pseg.com Testing Company: Maplewood Testing Services 200 Boyden Avenue

Maplewood NJ07040 Contact:Anthony Fortunato Phone:973-761-1005 Fax: 973-761-1015 Email:anthony.fortunato2@pseg.com

Air Permit Number: 2411 - NJDEP PI 18068 BOP080001 Permitted Source ID/Name: Sewaren Unit 1 U1 Permitted Maximum Process Rate: 1550 MMBtu/hr Max. Normal Operation Process Rate: 1550 MMBtu/hr Target Process Test Rate N/A

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Fuel oil fired (alternate natural gas) electric generating utility Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:110000801614

SCC / Description10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Tangential Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Exit 14.833 487 1579 4 14.833 24 157.7 157.7

Target Parameter Test Method Number of

Test Runs Test Run

DurationSample

Points Comments Location% H2O Method 1 - 4 3 180 0 Stack Exit Carbon Monoxide Method 10 3 120 0 Stack Exit Formaldehyde Method 0011 3 120 0 Stack Exit Regulation Description Compound Limit Unit NJAC 7:27-4.2a Total Particulate 335 lb/hr NJAC 7:27-27.7(a) (Based on annual weighted average of all valid stack emission tests performed for four consecutive quarters weighted by MW-hr) Mercury 3 mg/MW-hr



### Tuesday, February 22, 2011 Page 2 of 46

### PSEG Sewaren Unit 1
9/30/2010 2,3,7,8-TCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 Stack Exit OCDD Method 23 3 480 0 Stack Exit 2,3,7,8-TCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0 Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 Stack Exit OCDF Method 23 3 480 0 Stack Exit Other TCDD Method 23 0 Stack Exit Other PeCDD Method 23 0 Stack Exit Other HxCDD Method 23 0 Stack Exit Other HpCDD Method 23 0 Stack Exit Other TCDF Method 23 0 Stack Exit Other PeCDF Method 23 0 Stack Exit Other HxCDF Method 23 0 Stack Exit Other HpCDF Method 23 0 Stack Exit Total Dioxins Method 23 3 480 0 Stack Exit Total Furans Method 23 3 480 0 Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0 Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 Stack Exit 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 Stack Exit

2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 0 Stack Exit 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 0 Stack Exit 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 Stack Exit
Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Exit
Hydrogen Chloride Method 26 3 180 0 Stack Exit Hydrogen Chloride Method 26A 3 180 0 Stack Exit Hydrogen Fluoride Method 26 3 180 0 Stack Exit Hydrogen Fluoride Method 26A 3 180 0 Stack Exit Filterable Particulate OTM - 27/28 3 240 0 Stack Exit Total PM2.5 OTM - 27/28 3 240 0 Stack Exit Organic Condensible

Particulate OTM - 27/28 3 240 0 Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Stack Exit Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 240 0 Stack Exit



### Tuesday, February 22, 2011 Page 3 of 46

### PSEG Sewaren Unit 1
9/30/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. As per ICR, potassium permanganate impingers were not used as Hg was measured using Method 30B.

Total Particulate OTM - 27/28 3 240 0 Stack Exit Manganese Method 29 3 240 0 Stack Exit Nickel Method 29 3 240 0 Stack Exit Selenium Method 29 3 240 0 Stack Exit Filterable Particulate Method 29 3 240 0 Stack Exit Chromium Method 29 3 240 0 Stack Exit Cadmium Method 29 3 240 0 Stack Exit Lead Method 29 3 240 0 Stack Exit Beryllium Method 29 3 240 0 Stack Exit Arsenic Method 29 3 240 0 Stack Exit Filterable Particulate Method 29 3 240 0 Stack Exit Antimony Method 29 3 240 0 Stack Exit Cobalt Method 29 3 240 0 Stack Exit O2 Method 3A O2 3 120 0 Stack Exit Co2 Method 3A CO2 3 120 0 Stack Exit Total Particulate Method 5/OTM-28 3 240 0 Stack Exit Filterable Particulate Method 5/OTM-28 3 240 0 Stack Exit Organic Condensible

Particulate Method 5/OTM-28 3 240 0 Stack Exit

Filterable Particulate Method 5 3 240 0 Stack Exit Inorganic (Aqueous)

Condensible Part. Method 5/OTM-28 3 240 0 Stack Exit

Sulfur Dioxide Method 6C 3 180 0 Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0 Stack Exit



### Tuesday, February 22, 2011 Page 4 of 46

### PSEG Sewaren Unit 1
9/30/2010 Sampling / Stack Data Results Summary



### LocationStack Exit - Method 0011 Average Run Number 1 2 3
Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:20:00 AM 11:01:00 AM 1:55:00 PM

Run Finish Time 10:35:00 AM1:18:00 PM 4:17:00 PM Net Run Time, minutes 120 120 120 Dry Gas Meter Volume Sampled, dscf 81.459 82.627 84.185 82.757 Moisture Content of Stack Gas, % 5.67 5.62 5.56 5.617 Moisture Saturation at Stack Gas Temperature, % 87.05 90.10 96.11 91.087 Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Average Stack Gas Temperature, °F 204.79 206.38 209.63 206.933 Dry Volumetric Flow Rate, dry scfm 273,988.8 276,768.6 281,468.8277,408.733 Actual Wet Volumetric Flue Gas Flow Rate, acfm 368,168.3 373,349.3 380,913.7374,143.767 Percent Isokinetic of Sampling Rate, % 95.9 96.3 96.5 96.233 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 10 Average Run Number 1-1 1-2 1-3
Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:21:00 AM 11:02:00 AM 1:56:00 PM

Run Finish Time 10:26:00 AM1:01:00 PM 3:55:00 PM Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4258,298.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 5.67 3.48 5.56 4.903 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 5 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 23 Average Run Number 1 2 3
Test Date 7/13/2010 7/14/2010 7/15/2010 Run Start Time 4:15:00 AM 5:52:00 AM4:24:00 AM

Run Finish Time 8:00:00 PM9:35:00 PM 8:08:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 318.031 318.560 327.311 321.301 Moisture Content of Stack Gas, % 5.98 5.73 5.69 5.800 Moisture Saturation at Stack Gas Temperature, % 81.90 84.08 84.71 83.563 Carbon Dioxide, % 4.368 4.3 4.164 4.277 Oxygen, % 15.051 15.111 15.308 15.157 Average Stack Gas Temperature, °F 201.88 203.29 203.75 202.973 Dry Volumetric Flow Rate, dry scfm 269,247.0 267,786.6 274,234.8270,422.800 Actual Wet Volumetric Flue Gas Flow Rate, acfm 360,914.7 357,806.1 365,785.0361,501.933 Percent Isokinetic of Sampling Rate, % 97.3 98.0 96.3 97.200 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 25A Average Run Number 1-1 1-2 1-3
Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:21:00 AM 11:02:00 AM 1:56:00 PM

Run Finish Time 10:26:00 AM1:01:00 PM 3:55:00 PM Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Dry Volumetric Flow Rate, dry scfm 273988.8276768600 00 281468.89,225,805,15 2.533 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 5.67 3.48 5.56 4.903 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 6 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 26A Average Run Number 1 2 3
Test Date 7/13/2010 7/15/2010 7/15/2010 Run Start Time 5:16:00 PM5:03:00 PM 6:23:00 PM
Run Finish Time 6:27:00 PM6:12:00 PM 7:32:00 PM Net Run Time, minutes 60 60 60 Dry Gas Meter Volume Sampled, dscf 40.392 40.937 41.085 40.805 Moisture Content of Stack Gas, % 8.72 6.51 10.64 8.623 Moisture Saturation at Stack Gas Temperature, % 85.48 89.36 88.01 87.617 Carbon Dioxide, % 4.4 4.3 4.3 4.333 Oxygen, % 15 15.1 15.1 15.067 Average Stack Gas Temperature, °F 203.88 206.29 205.54 205.237 Dry Volumetric Flow Rate, dry scfm 269,064.2 271,280.3 263,326.2267,890.233 Actual Wet Volumetric Flue Gas Flow Rate, acfm 373,245.7 367,028.4 372,313.1370,862.400 Percent Isokinetic of Sampling Rate, % 98.9 97.4 100.7 99.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 29 Average Run Number 1 2 3
Test Date 7/13/2010 7/14/2010 7/14/2010 Run Start Time 10:39:00 AM 7:37:00 AM 2:50:00 PM

Run Finish Time 3:59:00 PM 12:52:00 PM 8:11:00 PM

Net Run Time, minutes 300 300 300 Dry Gas Meter Volume Sampled, dscf 197.362 200.864 196.485 198.237 Moisture Content of Stack Gas, % 6.63 6.22 5.96 6.270 Moisture Saturation at Stack Gas Temperature, % 78.30 83.27 80.75 80.773 Carbon Dioxide, % 4.341 4.339 4.315 4.332 Oxygen, % 15.124 15.091 15.072 15.096 Average Stack Gas Temperature, °F 199.38 202.67 201.21 201.087 Dry Volumetric Flow Rate, dry scfm 270,422.7 274,231.5 268,506.4271,053.533 Actual Wet Volumetric Flue Gas Flow Rate, acfm 366,095.8 369,100.9 359,360.4364,852.367 Percent Isokinetic of Sampling Rate, % 96.2 96.5 96.4 96.367 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 7 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 6C Average Run Number 1-1 1-2 1-3
Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:21:00 AM 11:02:00 AM 1:56:00 PM

Run Finish Time 10:26:00 AM1:01:00 PM 3:55:00 PM Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4258,298.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 5.67 3.48 5.56 4.903 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 6C 3 Average Run Number 3-1 3-2 3-3
Test Date 7/13/2010 7/15/2010 7/15/2010 Run Start Time 5:18:00 PM5:04:00 PM 6:23:00 PM Run Finish Time 6:24:00 PM6:03:00 PM 7:22:00 PM Carbon Dioxide, % 4.4 4.3 4.3 4.333 Oxygen, % 15 15.1 15.1 15.067 Dry Volumetric Flow Rate, dry scfm 252456.3 245857.5 238787.9245,700.567 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 4.83 6.51 10.64 7.327 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 8 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 7E Average Run Number 3-1 3-2 3-3
Test Date 7/13/2010 7/15/2010 7/15/2010 Run Start Time 5:18:00 PM5:04:00 PM 6:23:00 PM
Run Finish Time 6:24:00 PM6:03:00 PM 7:22:00 PM Carbon Dioxide, % 4.4 4.3 4.3 4.333 Oxygen, % 15 15.1 15.1 15.067 Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4258,298.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 5.67 3.48 5.56 4.903 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - OTM - 27/28 Average Run Number 1 2 3
Test Date 7/13/2010 7/14/2010 7/14/2010 Run Start Time 10:39:00 AM 7:37:00 AM 2:50:00 PM

Run Finish Time 4:40:00 PM1:21:00 PM 8:37:00 PM Net Run Time, minutes 335.42 330.1 330.63 Dry Gas Meter Volume Sampled, dscf 128.624 123.396 128.119 126.713 Moisture Content of Stack Gas, % 6.46 6.03 6.07 6.187 Moisture Saturation at Stack Gas Temperature, % 96.80 94.08 100.00 96.960 Carbon Dioxide, % 4.341 4.339 4.315 4.332 Oxygen, % 15.124 15.091 15.072 15.096 Average Stack Gas Temperature, °F 209.75 208.67 214.25 210.890 Dry Volumetric Flow Rate, dry scfm 273,497.8 263,453.0 270,634.2269,195.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 375,525.4 357,080.7 369,411.7367,339.267 Percent Isokinetic of Sampling Rate, % 103.6 104.9 105.8 104.767 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 9 of 46

### PSEG Sewaren Unit 1
9/30/2010 Emissions Summary



### Location: Stack Exit - Method 0011 Compound: Formaldehyde Average RunNumber 1 2 3 Mass_mg 0.23 0.12 0.25 0.200 lb/mmBtuO2 2.10E-04 1.10E-04 2.21E-04 0.000



### Location: Stack Exit - Method 10 Compound: Carbon Monoxide Average Run 1-1 1-2 1-3 Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000 gr/dscf 0.00E+00 0.00E+00 0.00E+00 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 mg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ppm 0.00E+00 0.00E+00 0.00E+00 0.000 ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000



### Location: Stack Exit - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 3 2 Mass_mg 0.0000000041 0.0000000024 0.0000000019 0.000 Elb/hr 4.59E-10 2.66E-10 2.11E-10 0.000 gr/dscf 1.99E-13 1.13E-13 9.20E-14 0.000 lb/mmBtuO2 9.33E-13 5.55E-13 4.36E-13 0.000 mg/dscm 4.55E-10 2.59E-10 2.11E-10 0.000 ng/dscm 4.55E-04 2.59E-04 2.11E-04 0.000 ng/dscm@7%O2 1.08E-03 6.44E-04 5.07E-04 0.001 ppm 2.57E-11 1.46E-11 1.19E-11 0.000 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 3 2 Mass_mg 0.000000004 0.0000000017 0.000000002 0.000 Elb/hr 4.48E-10 1.88E-10 2.22E-10 0.000 gr/dscf 1.94E-13 8.02E-14 9.69E-14 0.000 lb/mmBtuO2 9.11E-13 3.93E-13 4.59E-13 0.000 mg/dscm 4.44E-10 1.83E-10 2.22E-10 0.000 ng/dscm 4.44E-04 1.83E-04 2.22E-04 0.000 ng/dscm@7%O2 1.06E-03 4.55E-04 5.33E-04 0.001 ppm 2.61E-11 1.08E-11 1.30E-11 0.000 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 3 2 Mass_mg 0.0000000033 0.0000000018 0.0000000017 0.000 Elb/hr 3.70E-10 1.99E-10 1.89E-10 0.000 gr/dscf 1.60E-13 8.49E-14 8.24E-14 0.000 lb/mmBtuO2 7.51E-13 4.16E-13 3.90E-13 0.000



### Tuesday, February 22, 2011 Page 10 of 46

### PSEG Sewaren Unit 1
9/30/2010 mg/dscm 3.66E-10 1.94E-10 1.88E-10 0.000 ng/dscm 3.66E-04 1.94E-04 1.88E-04 0.000 ng/dscm@7%O2 8.70E-04 4.82E-04 4.51E-04 0.001 ppm 2.15E-11 1.14E-11 1.11E-11 0.000 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 3 2 Mass_mg 0.0000000065 0.0000000015 0.0000000016 0.000 Elb/hr 7.28E-10 1.66E-10 1.78E-10 0.000 gr/dscf 3.15E-13 7.07E-14 7.75E-14 0.000 lb/mmBtuO2 1.48E-12 3.47E-13 3.67E-13 0.000 mg/dscm 7.22E-10 1.62E-10 1.77E-10 0.000 ng/dscm 7.22E-04 1.62E-04 1.77E-04 0.000 ng/dscm@7%O2 1.72E-03 4.03E-04 4.25E-04 0.001 ppm 4.44E-11 9.96E-12 1.09E-11 0.000 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000036 0.0000000017 0.0000000015 0.000 Elb/hr 4.03E-10 1.89E-10 1.66E-10 0.000 gr/dscf 1.75E-13 8.24E-14 7.07E-14 0.000 lb/mmBtuO2 8.19E-13 3.90E-13 3.47E-13 0.000 mg/dscm 4.00E-10 1.88E-10 1.62E-10 0.000 ng/dscm 4.00E-04 1.88E-04 1.62E-04 0.000 ng/dscm@7%O2 9.51E-04 4.51E-04 4.03E-04 0.001 ppm 2.56E-11 1.21E-11 1.04E-11 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.000000007 0.0000000017 0.0000000016 0.000 Elb/hr 7.84E-10 1.89E-10 1.77E-10 0.000 gr/dscf 3.40E-13 8.24E-14 7.54E-14 0.000 lb/mmBtuO2 1.59E-12 3.90E-13 3.70E-13 0.000 mg/dscm 7.77E-10 1.88E-10 1.73E-10 0.000 ng/dscm 7.77E-04 1.88E-04 1.73E-04 0.000 ng/dscm@7%O2 1.85E-03 4.51E-04 4.30E-04 0.001 ppm 4.78E-11 1.16E-11 1.06E-11 0.000 

### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000035 0.0000000016 0.0000000014 0.000 Elb/hr 3.92E-10 1.78E-10 1.55E-10 0.000 gr/dscf 1.70E-13 7.75E-14 6.60E-14 0.000 lb/mmBtuO2 7.97E-13 3.67E-13 3.24E-13 0.000 mg/dscm 3.89E-10 1.77E-10 1.51E-10 0.000 ng/dscm 3.89E-04 1.77E-04 1.51E-04 0.000 ng/dscm@7%O2 9.24E-04 4.25E-04 3.75E-04 0.001 ppm 2.49E-11 1.14E-11 9.69E-12 0.000



### Tuesday, February 22, 2011 Page 11 of 46

### PSEG Sewaren Unit 1
9/30/2010 Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000065 0.0000000016 0.0000000015 0.000 Elb/hr 7.28E-10 1.78E-10 1.66E-10 0.000 gr/dscf 3.15E-13 7.75E-14 7.07E-14 0.000 lb/mmBtuO2 1.48E-12 3.67E-13 3.47E-13 0.000 mg/dscm 7.22E-10 1.77E-10 1.62E-10 0.000 ng/dscm 7.22E-04 1.77E-04 1.62E-04 0.000 ng/dscm@7%O2 1.72E-03 4.25E-04 4.03E-04 0.001 ppm 4.44E-11 1.09E-11 9.96E-12 0.000 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000043 0.000000002 0.0000000017 0.000 Elb/hr 4.82E-10 2.22E-10 1.88E-10 0.000 gr/dscf 2.09E-13 9.69E-14 8.02E-14 0.000 lb/mmBtuO2 9.79E-13 4.59E-13 3.93E-13 0.000 mg/dscm 4.78E-10 2.22E-10 1.83E-10 0.000 ng/dscm 4.78E-04 2.22E-04 1.83E-04 0.000 ng/dscm@7%O2 1.14E-03 5.33E-04 4.55E-04 0.001 ppm 3.06E-11 1.42E-11 1.18E-11 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000083 0.0000000018 0.0000000017 0.000 Elb/hr 9.29E-10 2.00E-10 1.88E-10 0.000 gr/dscf 4.03E-13 8.72E-14 8.02E-14 0.000 lb/mmBtuO2 1.89E-12 4.13E-13 3.93E-13 0.000 mg/dscm 9.22E-10 2.00E-10 1.83E-10 0.000 ng/dscm 9.22E-04 2.00E-04 1.83E-04 0.000 ng/dscm@7%O2 2.19E-03 4.80E-04 4.55E-04 0.001 ppm 6.22E-11 1.35E-11 1.24E-11 0.000 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000061 0.0000000019 0.0000000018 0.000 Elb/hr 6.83E-10 2.11E-10 1.99E-10 0.000 gr/dscf 2.96E-13 9.20E-14 8.49E-14 0.000 lb/mmBtuO2 1.39E-12 4.36E-13 4.16E-13 0.000 mg/dscm 6.77E-10 2.11E-10 1.94E-10 0.000 ng/dscm 6.77E-04 2.11E-04 1.94E-04 0.000 ng/dscm@7%O2 1.61E-03 5.07E-04 4.82E-04 0.001 ppm 4.79E-11 1.49E-11 1.37E-11 0.000 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.000000009 0.0000000064 0.0000000057 0.000 Elb/hr 1.01E-09 7.12E-10 6.32E-10 0.000



### Tuesday, February 22, 2011 Page 12 of 46

### PSEG Sewaren Unit 1
9/30/2010 gr/dscf 4.37E-13 3.10E-13 2.69E-13 0.000 lb/mmBtuO2 2.05E-12 1.47E-12 1.32E-12 0.000 mg/dscm 1.00E-09 7.10E-10 6.15E-10 0.000 ng/dscm 1.00E-03 7.10E-04 6.15E-04 0.001 ng/dscm@7%O2 2.38E-03 1.70E-03 1.53E-03 0.002 ppm 6.07E-11 4.31E-11 3.73E-11 0.000 

### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.00000013 0.000000097 0.000000083 0.000 Elb/hr 1.46E-08 1.08E-08 9.20E-09 0.000 gr/dscf 6.31E-12 4.70E-12 3.91E-12 0.000 lb/mmBtuO2 2.96E-11 2.23E-11 1.92E-11 0.000 mg/dscm 1.44E-08 1.08E-08 8.96E-09 0.000 ng/dscm 1.44E-02 1.08E-02 8.96E-03 0.011 ng/dscm@7%O2 3.42E-02 2.59E-02 2.23E-02 0.027 ppm 0.000 

### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.00000054 0.00000031 0.00000033 0.000 Elb/hr 6.05E-08 3.45E-08 3.66E-08 0.000 gr/dscf 2.62E-11 1.50E-11 1.56E-11 0.000 lb/mmBtuO2 1.23E-10 7.12E-11 7.63E-11 0.000 mg/dscm 6.00E-08 3.44E-08 3.56E-08 0.000 ng/dscm 6.00E-02 3.44E-02 3.56E-02 0.043 ng/dscm@7%O2 1.43E-01 8.26E-02 8.85E-02 0.105 ppm 0.000 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.000000044 0.000000032 0.000000025 0.000 Elb/hr 4.93E-09 3.56E-09 2.77E-09 0.000 gr/dscf 2.14E-12 1.55E-12 1.18E-12 0.000 lb/mmBtuO2 1.00E-11 7.35E-12 5.78E-12 0.000 mg/dscm 4.89E-09 3.55E-09 2.70E-09 0.000 ng/dscm 4.89E-03 3.55E-03 2.70E-03 0.004 ng/dscm@7%O2 1.16E-02 8.52E-03 6.71E-03 0.009 ppm 3.26E-10 2.36E-10 1.80E-10 0.000 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.000000035 0.000000021 0.000000022 0.000 Elb/hr 3.92E-09 2.34E-09 2.44E-09 0.000 gr/dscf 1.70E-12 1.02E-12 1.04E-12 0.000 lb/mmBtuO2 7.97E-12 4.82E-12 5.09E-12 0.000 mg/dscm 3.89E-09 2.33E-09 2.37E-09 0.000 ng/dscm 3.89E-03 2.33E-03 2.37E-03 0.003 ng/dscm@7%O2 9.24E-03 5.59E-03 5.89E-03 0.007 ppm 0.000



### Tuesday, February 22, 2011 Page 13 of 46

### PSEG Sewaren Unit 1
9/30/2010 Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.0000016 0.00000095 0.00000084 0.000 Elb/hr 1.79E-07 1.06E-07 9.31E-08 0.000 gr/dscf 7.76E-11 4.60E-11 3.96E-11 0.000 lb/mmBtuO2 3.64E-10 2.18E-10 1.94E-10 0.000 mg/dscm 1.78E-07 1.05E-07 9.06E-08 0.000 ng/dscm 1.78E-01 1.05E-01 9.06E-02 0.125 ng/dscm@7%O2 4.23E-01 2.52E-01 2.25E-01 0.300 ppm 0.000 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.000000024 0.000000012 0.00000002 0.000 Elb/hr 2.69E-09 1.33E-09 2.22E-09 0.000 gr/dscf 1.16E-12 5.81E-13 9.43E-13 0.000 lb/mmBtuO2 5.46E-12 2.76E-12 4.63E-12 0.000 mg/dscm 2.67E-09 1.33E-09 2.16E-09 0.000 ng/dscm 2.67E-03 1.33E-03 2.16E-03 0.002 ng/dscm@7%O2 6.35E-03 3.19E-03 5.37E-03 0.005 ppm 0.000 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000041 0.0000000019 0.0000000017 0.000 Elb/hr 4.59E-10 2.11E-10 1.88E-10 0.000 gr/dscf 1.99E-13 9.20E-14 8.02E-14 0.000 lb/mmBtuO2 9.33E-13 4.36E-13 3.93E-13 0.000 mg/dscm 4.55E-10 2.11E-10 1.83E-10 0.000 ng/dscm 4.55E-04 2.11E-04 1.83E-04 0.000 ng/dscm@7%O2 1.08E-03 5.07E-04 4.55E-04 0.001 ppm 2.92E-11 1.35E-11 1.18E-11 0.000 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000059 0.0000000019 0.0000000017 0.000 Elb/hr 6.61E-10 2.11E-10 1.88E-10 0.000 gr/dscf 2.86E-13 9.20E-14 8.02E-14 0.000 lb/mmBtuO2 1.34E-12 4.36E-13 3.93E-13 0.000 mg/dscm 6.55E-10 2.11E-10 1.83E-10 0.000 ng/dscm 6.55E-04 2.11E-04 1.83E-04 0.000 ng/dscm@7%O2 1.56E-03 5.07E-04 4.55E-04 0.001 ppm 4.63E-11 1.49E-11 1.30E-11 0.000 

### Compound: 2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000045 0.0000000016 0.0000000022 0.000 Elb/hr 5.04E-10 1.78E-10 2.44E-10 0.000



### Tuesday, February 22, 2011 Page 14 of 46

### PSEG Sewaren Unit 1
9/30/2010 gr/dscf 2.18E-13 7.75E-14 1.04E-13 0.000 lb/mmBtuO2 1.02E-12 3.67E-13 5.09E-13 0.000 mg/dscm 5.00E-10 1.77E-10 2.37E-10 0.000 ng/dscm 5.00E-04 1.77E-04 2.37E-04 0.000 ng/dscm@7%O2 1.19E-03 4.25E-04 5.89E-04 0.001 ppm 3.73E-11 1.32E-11 1.77E-11 0.000 

### Compound: 2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000055 0.0000000018 0.0000000027 0.000 Elb/hr 6.16E-10 2.00E-10 2.99E-10 0.000 gr/dscf 2.67E-13 8.72E-14 1.27E-13 0.000 lb/mmBtuO2 1.25E-12 4.13E-13 6.25E-13 0.000 mg/dscm 6.11E-10 2.00E-10 2.91E-10 0.000 ng/dscm 6.11E-04 2.00E-04 2.91E-04 0.000 ng/dscm@7%O2 1.45E-03 4.80E-04 7.23E-04 0.001 ppm 4.80E-11 1.57E-11 2.29E-11 0.000 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.0000000077 0.0000000048 0.0000000083 0.000 Elb/hr 8.62E-10 5.34E-10 9.20E-10 0.000 gr/dscf 3.74E-13 2.33E-13 3.91E-13 0.000 lb/mmBtuO2 1.75E-12 1.10E-12 1.92E-12 0.000 mg/dscm 8.55E-10 5.32E-10 8.96E-10 0.000 ng/dscm 8.55E-04 5.32E-04 8.96E-04 0.001 ng/dscm@7%O2 2.03E-03 1.28E-03 2.23E-03 0.002 ppm 0.000 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.0000000044 0.0000000072 0.0000000032 0.000 Elb/hr 4.93E-10 8.01E-10 3.55E-10 0.000 gr/dscf 2.14E-13 3.49E-13 1.51E-13 0.000 lb/mmBtuO2 1.00E-12 1.65E-12 7.40E-13 0.000 mg/dscm 4.89E-10 7.98E-10 3.45E-10 0.000 ng/dscm 4.89E-04 7.98E-04 3.45E-04 0.001 ng/dscm@7%O2 1.16E-03 1.92E-03 8.58E-04 0.001 ppm 0.000 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.000000059 0.000000042 0.000000067 0.000 Elb/hr 6.61E-09 4.67E-09 7.43E-09 0.000 gr/dscf 2.86E-12 2.03E-12 3.16E-12 0.000 lb/mmBtuO2 1.34E-11 9.64E-12 1.55E-11 0.000 mg/dscm 6.55E-09 4.66E-09 7.23E-09 0.000 ng/dscm 6.55E-03 4.66E-03 7.23E-03 0.006 ng/dscm@7%O2 1.56E-02 1.12E-02 1.80E-02 0.015 ppm 0.000



### Tuesday, February 22, 2011 Page 15 of 46

### PSEG Sewaren Unit 1
9/30/2010 Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.0000000031 0.0000000044 0.0000000032 0.000 Elb/hr 3.47E-10 4.89E-10 3.55E-10 0.000 gr/dscf 1.50E-13 2.13E-13 1.51E-13 0.000 lb/mmBtuO2 7.06E-13 1.01E-12 7.40E-13 0.000 mg/dscm 3.44E-10 4.88E-10 3.45E-10 0.000 ng/dscm 3.44E-04 4.88E-04 3.45E-04 0.000 ng/dscm@7%O2 8.18E-04 1.17E-03 8.58E-04 0.001 ppm 0.000 

### Compound: OCDD Average RunNumber 1 2 3 Mass_mg 0.0000000138 0.0000000135 0.0000000166 0.000 Elb/hr 1.55E-09 1.50E-09 1.84E-09 0.000 gr/dscf 6.70E-13 6.54E-13 7.83E-13 0.000 lb/mmBtuO2 3.14E-12 3.10E-12 3.84E-12 0.000 mg/dscm 1.53E-09 1.50E-09 1.79E-09 0.000 ng/dscm 1.53E-03 1.50E-03 1.79E-03 0.002 ng/dscm@7%O2 3.64E-03 3.60E-03 4.45E-03 0.004 ppm 8.02E-11 7.83E-11 9.37E-11 0.000 

### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.0000000073 0.0000000035 0.0000000037 0.000 Elb/hr 8.18E-10 3.89E-10 4.10E-10 0.000 gr/dscf 3.54E-13 1.70E-13 1.74E-13 0.000 lb/mmBtuO2 1.66E-12 8.04E-13 8.56E-13 0.000 mg/dscm 8.11E-10 3.88E-10 3.99E-10 0.000 ng/dscm 8.11E-04 3.88E-04 3.99E-04 0.001 ng/dscm@7%O2 1.93E-03 9.32E-04 9.92E-04 0.001 ppm 4.39E-11 2.10E-11 2.16E-11 0.000 

### Compound: Other HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000041 0.0000000019 0.0000000024 0.000 Elb/hr 4.59E-10 2.11E-10 2.66E-10 0.000 gr/dscf 1.99E-13 9.20E-14 1.13E-13 0.000 lb/mmBtuO2 9.33E-13 4.36E-13 5.55E-13 0.000 mg/dscm 4.55E-10 2.11E-10 2.59E-10 0.000 ng/dscm 4.55E-04 2.11E-04 2.59E-04 0.000 ng/dscm@7%O2 1.08E-03 5.07E-04 6.44E-04 0.001 ppm 2.57E-11 1.19E-11 1.46E-11 0.000 

### Compound: Other HpCDF Average RunNumber 2 3 1 Mass_mg 0.0000000022 0.0000000018 0.0000000043 0.000 Elb/hr 2.45E-10 1.99E-10 4.82E-10 0.000



### Tuesday, February 22, 2011 Page 16 of 46

### PSEG Sewaren Unit 1
9/30/2010 gr/dscf 1.07E-13 8.49E-14 2.09E-13 0.000 lb/mmBtuO2 5.05E-13 4.16E-13 9.79E-13 0.000 mg/dscm 2.44E-10 1.94E-10 4.78E-10 0.000 ng/dscm 2.44E-04 1.94E-04 4.78E-04 0.000 ng/dscm@7%O2 5.86E-04 4.82E-04 1.14E-03 0.001 ppm 1.43E-11 1.14E-11 2.81E-11 0.000 

### Compound: Other HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000096 0.0000000066 0.000000007 0.000 Elb/hr 1.08E-09 7.34E-10 7.76E-10 0.000 gr/dscf 4.66E-13 3.20E-13 3.30E-13 0.000 lb/mmBtuO2 2.19E-12 1.52E-12 1.62E-12 0.000 mg/dscm 1.07E-09 7.32E-10 7.55E-10 0.000 ng/dscm 1.07E-03 7.32E-04 7.55E-04 0.001 ng/dscm@7%O2 2.54E-03 1.76E-03 1.88E-03 0.002 ppm 6.56E-11 4.50E-11 4.65E-11 0.000 

### Compound: Other HxCDF Average RunNumber 2 3 1 Mass_mg 0.0000000018 0.0000000016 0.0000000039 0.000 Elb/hr 2.00E-10 1.77E-10 4.37E-10 0.000 gr/dscf 8.72E-14 7.54E-14 1.89E-13 0.000 lb/mmBtuO2 4.13E-13 3.70E-13 8.88E-13 0.000 mg/dscm 2.00E-10 1.73E-10 4.33E-10 0.000 ng/dscm 2.00E-04 1.73E-04 4.33E-04 0.000 ng/dscm@7%O2 4.80E-04 4.30E-04 1.03E-03 0.001 ppm 1.28E-11 1.11E-11 2.78E-11 0.000 

### Compound: Other PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000083 0.0000000029 0.0000000027 0.000 Elb/hr 9.29E-10 3.22E-10 2.99E-10 0.000 gr/dscf 4.03E-13 1.40E-13 1.27E-13 0.000 lb/mmBtuO2 1.89E-12 6.66E-13 6.25E-13 0.000 mg/dscm 9.22E-10 3.22E-10 2.91E-10 0.000 ng/dscm 9.22E-04 3.22E-04 2.91E-04 0.001 ng/dscm@7%O2 2.19E-03 7.73E-04 7.23E-04 0.001 ppm 6.22E-11 2.17E-11 1.97E-11 0.000 

### Compound: Other PeCDF Average RunNumber 1 2 3 Mass_mg 0.000000006 0.0000000019 0.0000000081 0.000 Elb/hr 6.72E-10 2.11E-10 8.98E-10 0.000 gr/dscf 2.91E-13 9.20E-14 3.82E-13 0.000 lb/mmBtuO2 1.37E-12 4.36E-13 1.87E-12 0.000 mg/dscm 6.66E-10 2.11E-10 8.74E-10 0.000 ng/dscm 6.66E-04 2.11E-04 8.74E-04 0.001 ng/dscm@7%O2 1.58E-03 5.07E-04 2.17E-03 0.001 ppm 4.71E-11 1.49E-11 6.17E-11 0.000



### Tuesday, February 22, 2011 Page 17 of 46

### PSEG Sewaren Unit 1
9/30/2010 Compound: Other TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000045 0.0000000022 0.0000000027 0.000 Elb/hr 5.04E-10 2.45E-10 2.99E-10 0.000 gr/dscf 2.18E-13 1.07E-13 1.27E-13 0.000 lb/mmBtuO2 1.02E-12 5.05E-13 6.25E-13 0.000 mg/dscm 5.00E-10 2.44E-10 2.91E-10 0.000 ng/dscm 5.00E-04 2.44E-04 2.91E-04 0.000 ng/dscm@7%O2 1.19E-03 5.86E-04 7.23E-04 0.001 ppm 3.73E-11 1.82E-11 2.18E-11 0.000 

### Compound: Other TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000055 0.0000000018 0.0000000044 0.000 Elb/hr 6.16E-10 2.00E-10 4.88E-10 0.000 gr/dscf 2.67E-13 8.72E-14 2.07E-13 0.000 lb/mmBtuO2 1.25E-12 4.13E-13 1.02E-12 0.000 mg/dscm 6.11E-10 2.00E-10 4.75E-10 0.000 ng/dscm 6.11E-04 2.00E-04 4.75E-04 0.000 ng/dscm@7%O2 1.45E-03 4.80E-04 1.18E-03 0.001 ppm 4.80E-11 1.57E-11 3.73E-11 0.000 

### Compound: Total Dioxins Average RunNumber 1 2 3 Mass_mg 0.0000000772 0.0000000373 0.0000000423 0.000 Elb/hr 8.65E-09 4.15E-09 4.69E-09 0.000 gr/dscf 3.75E-12 1.81E-12 1.99E-12 0.000 lb/mmBtuO2 1.76E-11 8.56E-12 9.79E-12 0.000 mg/dscm 8.57E-09 4.14E-09 4.56E-09 0.000 ng/dscm 8.57E-03 4.14E-03 4.56E-03 0.006 ng/dscm@7%O2 2.04E-02 9.94E-03 1.13E-02 0.014 ppm 0.000 

### Compound: Total Furans Average RunNumber 1 2 3 Mass_mg 0.0000000673 0.0000000277 0.0000000356 0.000 Elb/hr 7.54E-09 3.08E-09 3.95E-09 0.000 gr/dscf 3.27E-12 1.34E-12 1.68E-12 0.000 lb/mmBtuO2 1.53E-11 6.36E-12 8.24E-12 0.000 mg/dscm 7.47E-09 3.07E-09 3.84E-09 0.000 ng/dscm 7.47E-03 3.07E-03 3.84E-03 0.005 ng/dscm@7%O2 1.78E-02 7.37E-03 9.55E-03 0.012 ppm 0.000



### Location: Stack Exit - Method 25A 

### Compound: Total organic compounds (TOC) as Average Run 1-1 1-2 1-3 Elb/hr 3.02E-01 3.31E+04 7.67E-01 11,033.690


### Tuesday, February 22, 2011 Page 18 of 46

### PSEG Sewaren Unit 1
9/30/2010 gr/dscf 1.28E-04 1.39E-04 3.18E-04 0.000 lb/mmBtuO2 6.18E-04 6.83E-04 1.53E-03 0.001 mg/dscm 2.94E-01 3.19E-01 7.27E-01 0.447 ppm 1.60E-01 1.74E-01 3.97E-01 0.244 ppm@7%O2 3.90E-01 4.32E-01 9.68E-01 0.597



### Location: Stack Exit - Method 26A Compound: Hydrogen Chloride Average RunNumber 2 3 1 Mass_mg 1.8 3.5 0.94 2.080 Elb/hr 1.58E+00 2.97E+00 8.28E-01 1.793 lb/mmBtuO2 3.21E-03 6.22E-03 1.67E-03 0.004 mg/dscm 1.55E+00 3.01E+00 8.22E-01 1.794 mg/dscm@7%O2 3.71E+00 7.21E+00 1.94E+00 4.287 

### Compound: Hydrogen Fluoride Average RunNumber 2 3 1 Mass_mg 1.3 0.22 0.22 0.580 Elb/hr 1.14E+00 1.87E-01 1.94E-01 0.507 lb/mmBtuO2 2.32E-03 3.91E-04 3.91E-04 0.001 mg/dscm 1.12E+00 1.89E-01 1.92E-01 0.500 mg/dscm@7%O2 2.68E+00 4.53E-01 4.52E-01 1.195



### Location: Stack Exit - Method 29 Compound: Antimony Average RunNumber 3 1 2 Mass_mg 0.1912 0.1962 0.19425 0.194 Elb/hr 3.46E-02 3.56E-02 3.51E-02 0.035 lb/mmBtuO2 7.07E-05 7.29E-05 7.05E-05 0.000 mg/dscm 3.44E-02 3.51E-02 3.42E-02 0.035 mg/dscm@7%O2 8.20E-02 8.45E-02 8.18E-02 0.083 

### Compound: Arsenic Average RunNumber 3 1 2 Mass_mg 0.0053 0.0057 0.0053 0.005 Elb/hr 9.58E-04 1.03E-03 9.57E-04 0.001 lb/mmBtuO2 1.96E-06 2.12E-06 1.92E-06 0.000 mg/dscm 9.53E-04 1.02E-03 9.32E-04 0.001 mg/dscm@7%O2 2.27E-03 2.45E-03 2.23E-03 0.002 

### Compound: Beryllium Average RunNumber 3 1 2 Mass_mg 0.00153 0.00183 0.00183 0.002 Elb/hr 2.77E-04 3.32E-04 3.30E-04 0.000 lb/mmBtuO2 5.66E-07 6.80E-07 6.64E-07 0.000 mg/dscm 2.75E-04 3.27E-04 3.22E-04 0.000 mg/dscm@7%O2 6.56E-04 7.87E-04 7.70E-04 0.001



### Tuesday, February 22, 2011 Page 19 of 46

### PSEG Sewaren Unit 1
9/30/2010 Compound: Cadmium Average RunNumber 3 1 2 Mass_mg 0.00035 0.00035 0.00035 0.000 Elb/hr 6.33E-05 6.34E-05 6.32E-05 0.000 lb/mmBtuO2 1.29E-07 1.30E-07 1.27E-07 0.000 mg/dscm 6.29E-05 6.26E-05 6.15E-05 0.000 mg/dscm@7%O2 1.50E-04 1.51E-04 1.47E-04 0.000 

### Compound: Chromium Average RunNumber 3 1 2 Mass_mg 0.00553 0.00577 0.00466 0.005 Elb/hr 1.00E-03 1.05E-03 8.42E-04 0.001 lb/mmBtuO2 2.04E-06 2.14E-06 1.69E-06 0.000 mg/dscm 9.94E-04 1.03E-03 8.19E-04 0.001 mg/dscm@7%O2 2.37E-03 2.48E-03 1.96E-03 0.002 

### Compound: Cobalt Average RunNumber 3 1 2 Mass_mg 0.081375 0.086368 0.081875 0.083 Elb/hr 1.47E-02 1.57E-02 1.48E-02 0.015 lb/mmBtuO2 3.01E-05 3.21E-05 2.97E-05 0.000 mg/dscm 1.46E-02 1.55E-02 1.44E-02 0.015 mg/dscm@7%O2 3.48E-02 3.73E-02 3.45E-02 0.036 

### Compound: Filterable Particulate Average RunNumber 3 1 2 Mass_mg 20.6 19.4 21.5 20.500 Elb/hr 3.72E+00 3.52E+00 3.88E+00 3.707 lb/mmBtuO2 7.62E-03 7.21E-03 7.80E-03 0.008 mg/dscm 3.70E+00 3.47E+00 3.78E+00 3.650 mg/dscm@7%O2 8.82E+00 8.35E+00 9.04E+00 8.737 

### Compound: Lead Average RunNumber 3 1 2 Mass_mg 0.01579 0.01593 0.01577 0.016 Elb/hr 2.85E-03 2.89E-03 2.85E-03 0.003 lb/mmBtuO2 5.84E-06 5.92E-06 5.72E-06 0.000 mg/dscm 2.84E-03 2.85E-03 2.77E-03 0.003 mg/dscm@7%O2 6.77E-03 6.86E-03 6.63E-03 0.007 

### Compound: Manganese Average RunNumber 3 1 2 Mass_mg 0.1389 0.1403 0.1396 0.140 Elb/hr 2.51E-02 2.54E-02 2.52E-02 0.025 lb/mmBtuO2 5.14E-05 5.21E-05 5.07E-05 0.000 mg/dscm 2.50E-02 2.51E-02 2.45E-02 0.025 mg/dscm@7%O2 5.96E-02 6.04E-02 5.86E-02 0.060



### Tuesday, February 22, 2011 Page 20 of 46

### PSEG Sewaren Unit 1
9/30/2010 Compound: Nickel Average RunNumber 3 1 2 Mass_mg 1.4786 1.555 1.4559 1.497 Elb/hr 2.67E-01 2.82E-01 2.63E-01 0.271 lb/mmBtuO2 5.47E-04 5.78E-04 5.28E-04 0.001 mg/dscm 2.66E-01 2.78E-01 2.56E-01 0.267 mg/dscm@7%O2 6.34E-01 6.69E-01 6.13E-01 0.639 

### Compound: Selenium Average RunNumber 3 1 2 Mass_mg 0.0042 0.0035 0.0043 0.004 Elb/hr 7.59E-04 6.34E-04 7.77E-04 0.001 lb/mmBtuO2 1.55E-06 1.30E-06 1.56E-06 0.000 mg/dscm 7.55E-04 6.26E-04 7.56E-04 0.001 mg/dscm@7%O2 1.80E-03 1.51E-03 1.81E-03 0.002



### Location: Stack Exit - Method 6C Compound: Sulfur Dioxide Average Run 1-1 1-2 1-3 Elb/hr 1.19E+02 1.21E+02 1.22E+02 120.667 lb/mmBtuO2 2.64E-01 2.65E-01 2.64E-01 0.264 mg/dscm 1.26E+02 1.24E+02 1.26E+02 125.333 mg/dscm@7%O2 3.07E+02 3.08E+02 3.07E+02 307.333 ppm 4.72E+01 4.65E+01 4.71E+01 46.933 ppm@7%O2 1.15E+02 1.15E+02 1.15E+02 115.000



### Location: Stack Exit - Method 6C 3 Compound: Sulfur Dioxide Average Run 3-1 3-2 3-3 Elb/hr 1.20E+02 1.16E+02 1.13E+02 116.333 lb/mmBtuO2 2.58E-01 2.60E-01 2.61E-01 0.260 mg/dscm 1.27E+02 1.26E+02 1.26E+02 126.333 mg/dscm@7%O2 2.99E+02 3.02E+02 3.02E+02 301.000 ppm 4.76E+01 4.72E+01 4.74E+01 47.400 ppm@7%O2 1.12E+02 1.13E+02 1.14E+02 113.000



### Location: Stack Exit - Method 7E Compound: Nitrogen oxides (NOx) Average Run 3-1 3-2 3-3 Elb/hr 1.09E+02 1.21E+02 1.23E+02 117.667 lb/mmBtuO2 2.33E-01 2.55E-01 2.60E-01 0.249 mg/dscm 1.15E+02 1.24E+02 1.26E+02 121.667 mg/dscm@7%O2 2.71E+02 2.97E+02 3.02E+02 290.000 ppm 6.00E+01 6.46E+01 6.58E+01 63.467 ppm@7%O2 1.41E+02 1.55E+02 1.58E+02 151.333



### Location: Stack Exit - OTM - 27/28
Tuesday, February 22, 2011 Page 21 of 46

### PSEG Sewaren Unit 1
9/30/2010

Process Run Data Compound: Filterable Particulate Average RunNumber 2 3 1 Mass_mg 16.9 18.6 14.5 16.667 Elb/hr 4.77E+00 5.20E+00 4.08E+00 4.683 gr/dscf 2.11E-03 2.24E-03 1.74E-03 0.002 lb/mmBtuO2 9.98E-03 1.05E-02 8.26E-03 0.010 mg/dscm 4.84E+00 5.13E+00 3.98E+00 4.650 ppm #Num!



### Tuesday, February 22, 2011 Page 22 of 46

### PSEG Sewaren Unit 1
9/30/2010 Process Run Data



### Run Name Value UOM Comments Target Value 2 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 Run 1 M0011 Start 7/15/2010 8:20 End 7/15/2010 10:35 0



### 2 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 1 M0011 Start 7/15/2010 8:20 End 7/15/2010 10:35 0

2 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 1 M0011 Start 7/15/2010 8:20 End 7/15/2010 10:35 0

3 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 Runs 1-4 M0031 Start 7/15/2010 8:21 End 7/15/2010 10:21 0

3 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Runs 1-4 M0031 Start 7/15/2010 8:21 End 7/15/2010 10:21 0

3 Unit Net Electric Generation 30 MWh SEW1 Group 1 Runs 1-4 M0031 Start 7/15/2010 8:21 End 7/15/2010 10:21 0



### 4 Fuel Oil Firing Rate 2601 gal/hr SEW1 Group 1 Run 1 M18 (CH4) Start 7/15/2010 17:38 End 7/15/2010 17:42 0

4 Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 1 M18 (CH4) Start 7/15/2010 17:38 End 7/15/2010 17:42 0

4 Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 1 M18 (CH4) Start 7/15/2010 17:38 End 7/15/2010 17:42 0

Tuesday, February 22, 2011 Page 23 of 46

### PSEG Sewaren Unit 1
9/30/2010 5 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 Run 1 M6C (SO2) Start 7/15/2010 8:21 End 7/15/2010 10:26 0



### 5 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 1 M6C (SO2) Start 7/15/2010 8:21 End 7/15/2010 10:26 0

5 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 1 M6C (SO2) Start 7/15/2010 8:21 End 7/15/2010 10:26 0

6 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 Run 1 M10 (CO) Start 7/15/2010 8:21 End 7/15/2010 10:26 0

6 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 1 M10 (CO) Start 7/15/2010 8:21 End 7/15/2010 10:26 0

6 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 1 M10 (CO) Start 7/15/2010 8:21 End 7/15/2010 10:26 0



### 7 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 Run 1 M25A (TOC as propane) Start 7/15/2010 8:21 End 7/15/2010 10:26 0

7 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 1 M25A (TOC as propane) Start 7/15/2010 8:21 End 7/15/2010 10:26 0

7 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 1 M25A (TOC as propane) Start 7/15/2010 8:21 End 7/15/2010 10:26 0



### Tuesday, February 22, 2011 Page 24 of 46

### PSEG Sewaren Unit 1
9/30/2010 8 Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 1 Run 2 M0010 Start 7/15/2010 11:01 End 7/15/2010 13:15 0



### 8 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 2 M0010 Start 7/15/2010 11:01 End 7/15/2010 13:15 0

8 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 2 M0010 Start 7/15/2010 11:01 End 7/15/2010 13:15 0

9 Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 Run 2 M10 (CO) Start 7/15/2010 11:02 End 7/15/2010 13:01 0

9 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 2 M10 (CO) Start 7/15/2010 11:02 End 7/15/2010 13:01 0

9 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 2 M10 (CO) Start 7/15/2010 11:02 End 7/15/2010 13:01 0



### 10Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 1 Run 2 M0011 Start 7/15/2010 11:01 End 7/15/2010 13:18 0

10Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 2 M0011 Start 7/15/2010 11:01 End 7/15/2010 13:18 0

10Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 2 M0011 Start 7/15/2010 11:01 End 7/15/2010 13:18 0

11Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 1 Runs 5-8 M0031 Start 7/15/2010 11:03 End 7/15/2010 13:10 0



### Tuesday, February 22, 2011 Page 25 of 46

### PSEG Sewaren Unit 1
9/30/2010 11Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Runs 5-8 M0031 Start 7/15/2010 11:03 End 7/15/2010 13:10 0



### 11Unit Net Electric Generation 30 MWh SEW1 Group 1 Runs 5-8 M0031 Start 7/15/2010 11:03 End 7/15/2010 13:10 0

12Fuel Oil Firing Rate 2604 gal/hr SEW1 Group 1 Run 2 M18 (CH4) Start 7/15/2010 17:48 End 7/15/2010 17:51 0

12Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 2 M18 (CH4) Start 7/15/2010 17:48 End 7/15/2010 17:51 0

12Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 2 M18 (CH4) Start 7/15/2010 17:48 End 7/15/2010 17:51 0

13Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 Run 2 M6C (SO2) Start 7/15/2010 11:02 End 7/15/2010 13:01 0



### 13Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 2 M6C (SO2) Start 7/15/2010 11:02 End 7/15/2010 13:01 0

13Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 2 M6C (SO2) Start 7/15/2010 11:02 End 7/15/2010 13:01 0

14Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 Run 2 M25A (TOC as propane) Start 7/15/2010 11:02 End 7/15/2010 13:01 0



### Tuesday, February 22, 2011 Page 26 of 46

### PSEG Sewaren Unit 1
9/30/2010 14Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 2 M25A (TOC as propane) Start 7/15/2010 11:02 End 7/15/2010 13:01 0



### 14Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 2 M25A (TOC as propane) Start 7/15/2010 11:02 End 7/15/2010 13:01 0

15Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 Run 3 M0010 Start 7/15/2010 13:55 End 7/15/2010 16:18 0

15Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 3 M0010 Start 7/15/2010 13:55 End 7/15/2010 16:18 0



### 15Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 3 M0010 Start 7/15/2010 13:55 End 7/15/2010 16:18 0

16Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 Run 3 M0011 Start 7/15/2010 13:55 End 7/15/2010 16:17 0

16Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 3 M0011 Start 7/15/2010 13:55 End 7/15/2010 16:17 0

16Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 3 M0011 Start 7/15/2010 13:55 End 7/15/2010 16:17 0

17Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 Runs 9-12 M0031 Start 7/15/2010 13:55 End 7/15/2010 16:05 0



### Tuesday, February 22, 2011 Page 27 of 46

### PSEG Sewaren Unit 1
9/30/2010 17Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Runs 9-12 M0031 Start 7/15/2010 13:55 End 7/15/2010 16:05 0



### 17Unit Net Electric Generation 31 MWh SEW1 Group 1 Runs 9-12 M0031 Start 7/15/2010 13:55 End 7/15/2010 16:05 0

18Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 1 Run 3 M18 (CH4) Start 7/15/2010 17:57 End 7/15/2010 18:00 0

18Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 3 M18 (CH4) Start 7/15/2010 17:57 End 7/15/2010 18:00 0

18Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 3 M18 (CH4) Start 7/15/2010 17:57 End 7/15/2010 18:00 0

19Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 Run 3 M6C (SO2) Start 7/15/2010 13:56 End 7/15/2010 15:55 0



### 19Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 3 M6C (SO2) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

19Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 3 M6C (SO2) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

20Fuel Oil Firing Rate 2595 gal/hr SEW1 Group 2 Run 1 M23 Start 7/13/2010 20:00 End 7/14/2010 4:15 0

20Unit Gross Electrical Output 32 Mwe SEW1 Group 2 Run 1 M23 Start 7/13/2010 20:00 End 7/14/2010 4:15 0



### Tuesday, February 22, 2011 Page 28 of 46

### PSEG Sewaren Unit 1
9/30/2010 20Unit Net Electric Generation 30 MWh SEW1 Group 2 Run 1 M23 Start 7/13/2010 20:00 End 7/14/2010 4:15 0



### 21Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 Run 3 M10 (CO) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

21Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 3 M10 (CO) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

21Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 3 M10 (CO) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

22Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 1 Run 3 M25A (TOC as propane) Start 7/15/2010 13:56 End 7/15/2010 15:55 0



### 22Unit Gross Electrical Output 33 Mwe SEW1 Group 1 Run 3 M25A (TOC as propane) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

22Unit Net Electric Generation 31 MWh SEW1 Group 1 Run 3 M25A (TOC as propane) Start 7/15/2010 13:56 End 7/15/2010 15:55 0

23Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 2 Run 2 M23 Start 7/14/2010 21:35 End 7/15/2010 5:52 0



### 23Unit Gross Electrical Output 32 Mwe SEW1 Group 2 Run 2 M23 Start 7/14/2010 21:35 End 7/15/2010 5:52 0

Tuesday, February 22, 2011 Page 29 of 46

### PSEG Sewaren Unit 1
9/30/2010 23Unit Net Electric Generation 30 MWh SEW1 Group 2 Run 2 M23 Start 7/14/2010 21:35 End 7/15/2010 5:52 0



### 24Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 2 Run 3 M23 Start 7/15/2010 20:08 End 7/16/2010 4:24 0

24Unit Gross Electrical Output 32 Mwe SEW1 Group 2 Run 3 M23 Start 7/15/2010 20:08 End 7/16/2010 4:24 0

24Unit Net Electric Generation 30 MWh SEW1 Group 2 Run 3 M23 Start 7/15/2010 20:08 End 7/16/2010 4:24 0

25Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 3 Run 1 M26A Start 7/13/2010 17:16 End 7/13/2010 18:27 0

25Unit Gross Electrical Output 32 Mwe SEW1 Group 3 Run 1 M26A Start 7/13/2010 17:16 End 7/13/2010 18:27 0



### 25Unit Net Electric Generation 30 MWh SEW1 Group 3 Run 1 M26A Start 7/13/2010 17:16 End 7/13/2010 18:27 0

26Fuel Oil Firing Rate 2608 gal/hr SEW1 Group 3 Run 1 M6C (SO2) Start 7/15/2010 17:18 End 7/15/2010 18:24 0

26Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 1 M6C (SO2) Start 7/15/2010 17:18 End 7/15/2010 18:24 0

26Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 1 M6C (SO2) Start 7/15/2010 17:18 End 7/15/2010 18:24 0



### Tuesday, February 22, 2011 Page 30 of 46

### PSEG Sewaren Unit 1
9/30/2010 27Fuel Oil Firing Rate 2608 gal/hr SEW1 Group 3 Run 1 M7E (NOx) Start 7/15/2010 17:18 End 7/15/2010 18:24 0



### 27Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 1 M7E (NOx) Start 7/15/2010 17:18 End 7/15/2010 18:24 0

27Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 1 M7E (NOx) Start 7/15/2010 17:18 End 7/15/2010 18:24 0

28Fuel Oil Firing Rate 2609 gal/hr SEW1 Group 3 Run 2 M26A Start 7/15/2010 17:03 End 7/15/2010 18:12 0

28Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 2 M26A Start 7/15/2010 17:03 End 7/15/2010 18:12 0

28Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 2 M26A Start 7/15/2010 17:03 End 7/15/2010 18:12 0



### 29Fuel Oil Firing Rate 2610 gal/hr SEW1 Group 3 Run 2 M6C (SO2) Start 7/15/2010 17:04 End 7/15/2010 18:03 0

29Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 2 M6C (SO2) Start 7/15/2010 17:04 End 7/15/2010 18:03 0

29Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 2 M6C (SO2) Start 7/15/2010 17:04 End 7/15/2010 18:03 0

30Fuel Oil Firing Rate 2610 gal/hr SEW1 Group 3 Run 2 M7E (NOx) Start 7/15/2010 17:04 End 7/15/2010 18:03 0



### Tuesday, February 22, 2011 Page 31 of 46

### PSEG Sewaren Unit 1
9/30/2010 30Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 2 M7E (NOx) Start 7/15/2010 17:04 End 7/15/2010 18:03 0



### 30Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 2 M7E (NOx) Start 7/15/2010 17:04 End 7/15/2010 18:03 0

31Fuel Oil Firing Rate 2612 gal/hr SEW1 Group 3 Run 3 M26A Start 7/15/2010 18:23 End 7/15/2010 19:32 0

31Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 3 M26A Start 7/15/2010 18:23 End 7/15/2010 19:32 0

31Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 3 M26A Start 7/15/2010 18:23 End 7/15/2010 19:32 0

32Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 3 Run 3 M6C (SO2) Start 7/15/2010 18:23 End 7/15/2010 19:22 0



### 32Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 3 M6C (SO2) Start 7/15/2010 18:23 End 7/15/2010 19:22 0

32Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 3 M6C (SO2) Start 7/15/2010 18:23 End 7/15/2010 19:22 0

33Fuel Oil Firing Rate 2611 gal/hr SEW1 Group 3 Run 3 M7E (NOx) Start 7/15/2010 18:23 End 7/15/2010 19:22 0

33Unit Gross Electrical Output 33 Mwe SEW1 Group 3 Run 3 M7E (NOx) Start 7/15/2010 18:23 End 7/15/2010 19:22 0



### Tuesday, February 22, 2011 Page 32 of 46

### PSEG Sewaren Unit 1
9/30/2010 33Unit Net Electric Generation 31 MWh SEW1 Group 3 Run 3 M7E (NOx) Start 7/15/2010 18:23 End 7/15/2010 19:22 0



### 34Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 4 Run 2 M29 Start 7/14/2010 7:37 End 7/14/2010 12:52 0

34Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 2 M29 Start 7/14/2010 7:37 End 7/14/2010 12:52 0

34Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 2 M29 Start 7/14/2010 7:37 End 7/14/2010 12:52 0

35Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 4 Run 2 OTM027/028 Start 7/14/2010 7:37 End 7/14/2010 13:21 0



### 35Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 2 OTM027/028 Start 7/14/2010 7:37 End 7/14/2010 13:21 0

35Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 2 OTM027/028 Start 7/14/2010 7:37 End 7/14/2010 13:21 0

36Fuel Oil Firing Rate 2592 gal/hr SEW1 Group 4 Run 2 M30B Start 7/14/2010 7:37 End 7/14/2010 13:37 0



### 36Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 2 M30B Start 7/14/2010 7:37 End 7/14/2010 13:37 0

Tuesday, February 22, 2011 Page 33 of 46

### PSEG Sewaren Unit 1
9/30/2010 36Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 2 M30B Start 7/14/2010 7:37 End 7/14/2010 13:37 0



### 37Fuel Oil Firing Rate 2590 gal/hr SEW1 Group 4 Run 3 M29 Start 7/14/2010 14:50 End 7/14/2010 20:11 0

37Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 3 M29 Start 7/14/2010 14:50 End 7/14/2010 20:11 0

37Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 3 M29 Start 7/14/2010 14:50 End 7/14/2010 20:11 0

38Fuel Oil Firing Rate 2590 gal/hr SEW1 Group 4 Run 3 OTM027/028 Start 7/14/2010 14:50 End 7/14/2010 20:37 0



### 38Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 3 OTM027/028 Start 7/14/2010 14:50 End 7/14/2010 20:37 0

38Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 3 OTM027/028 Start 7/14/2010 14:50 End 7/14/2010 20:37 0

39Fuel Oil Firing Rate 2590 gal/hr SEW1 Group 4 Run 3 M30B Start 7/14/2010 14:31 End 7/14/2010 20:31 0



### 39Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 3 M30B Start 7/14/2010 14:31 End 7/14/2010 20:31 0

Tuesday, February 22, 2011 Page 34 of 46

### PSEG Sewaren Unit 1
9/30/2010 39Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 3 M30B Start 7/14/2010 14:31 End 7/14/2010 20:31 0



### 40Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 4 Run 1 M29 Start 7/13/2010 10:39 End 7/13/2010 15:59 0

40Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 1 M29 Start 7/13/2010 10:39 End 7/13/2010 15:59 0

40Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 1 M29 Start 7/13/2010 10:39 End 7/13/2010 15:59 0

41Fuel Oil Firing Rate 2597 gal/hr SEW1 Group 4 Run 1 OTM027/028 Start 7/13/2010 10:39 End 7/13/2010 16:40 0



### 41Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 1 OTM027/028 Start 7/13/2010 10:39 End 7/13/2010 16:40 0

41Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 1 OTM027/028 Start 7/13/2010 10:39 End 7/13/2010 16:40 0

42Fuel Oil Firing Rate 2596 gal/hr SEW1 Group 4 Run 1 M30B Start 7/13/2010 10:41 End 7/13/2010 16:41 0



### 42Unit Gross Electrical Output 32 Mwe SEW1 Group 4 Run 1 M30B Start 7/13/2010 10:41 End 7/13/2010 16:41 0

Tuesday, February 22, 2011 Page 35 of 46

### PSEG Sewaren Unit 1
9/30/2010

APCD Run Data

Process Lab Run Data 42Unit Net Electric Generation 30 MWh SEW1 Group 4 Run 1 M30B Start 7/13/2010 10:41 End 7/13/2010 16:41 0



### 1 Heat Input 0 Million Btus/million BTU using O2 0
1 Fuel Oil Firing Rate 2593 gal/hr SEW1 Group 1 Run 1 M0010 Start 7/15/2010 8:20 End 7/15/2010 10:36 0

1 Unit Gross Electrical Output 32 Mwe SEW1 Group 1 Run 1 M0010 Start 7/15/2010 8:20 End 7/15/2010 10:36 0

1 Unit Net Electric Generation 30 MWh SEW1 Group 1 Run 1 M0010 Start 7/15/2010 8:20 End 7/15/2010 10:36 0

Run Name ValueUOM Comments 

### 1 Fuel Higher Heating Value 0 Btu/lb 1 Fuel Moisture 0 % 1 Fuel Mercury Content 0 ppm 

### 1 Fuel Cadmium Content 0 ppm 1 Ultimate/Proximate Analysis 0 1 Fuel Nickel Content 0 ppm 1 Fuel Arsenic Content 0 ppm 

### 1 Fuel Chromium Content 0 ppm 1 Fuel Beryllium Content 0 ppm 1 Fuel Lead Content 0 ppm 

### 1 Fuel Manganese Content 0 ppm 1 Fuel Chlorine Content 0 ppm 1 Fuel Fluorine Content 0 ppm



### Tuesday, February 22, 2011 Page 36 of 46

### PSEG Sewaren Unit 1
9/30/2010 Sampling / Stack Data Results Detail



### LocationStack Exit - Method 0011 Average Run Number 1 2 3 Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:20:00 AM11:01:00 AM 1:55:00 PM Run Finish Time 10:35:00 AM1:18:00 PM 4:17:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 120 120 120 Nozzle Diameter, inches 0.286 0.286 0.286 0.286 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988 Barometric Pressure, inches of Mercury 29.745 29.68 29.715 29.713 Average Orifice Meter Differential, inches H2O 1.67 1.71 1.76 1.713 Dry Gas Meter Volume Sampled, cubic feet 85.685 88.199 90.044 87.976 Average Dry Gas Meter Temperature, °F 87.88 94.83 96.67 93.127 Dry Gas Meter Volume Sampled, dscf 81.459 82.627 84.185 82.757 Total Moisture Liquid collected, g 104.2 104.6 105.3 104.700 Volume of Water Vapor, standard cubic feet 4.90 4.92 4.96 4.927 Moisture Content of Stack Gas, % 5.67 5.62 5.56 5.617 Moisture Saturation at Stack Gas Temperature, % 87.05 90.10 96.11 91.087 Dry Mole Fraction 0.9433 0.9438 0.9444 0.944 Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Carbon Monoxide & Nitrogen, % 80.5 80.5 80.5 80.500 Fuel Factor 1.33 1.33 1.33 Dry Molecular Weight, lb/lb-Mole 29.30 29.28 29.30 29.293 Wet Molecular weight, lb/lb-Mole 28.66 28.65 28.67 28.660 Flue Gas Static Pressure, inches of H2O -0.29 -0.29 -0.29 -0.290 Absolute Flue Gas Pressure, inches of Mercury 29.72 29.66 29.69 29.690 Average Stack Gas Temperature, °F 204.79 206.38 209.63 206.933 Average Velocity Head, inches of H2O 0.3137310707 431510.321087307

3006180.333166737

610149 0.323
Average Stack Gas Velocity, feet/second 35.53 36.03 36.76 36.107 Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703 Dry Volumetric Flow Rate, dry scfm 273,988.8 276,768.6 281,468.8277,408.733 Actual Wet Volumetric Flue Gas Flow Rate, acfm 368,168.3 373,349.3 380,913.7374,143.767 Percent Isokinetic of Sampling Rate, % 95.9 96.3 96.5 96.233 Percent Excess Air, % 251.2 257.1 251.2 253.167 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.833 14.833 14.833 Rectangular Duct Width, inches 157.7 157.7 157.7 Rectangular Duct Length, inches 157.7 157.7 157.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 37 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 10 Average Run Number 1-1 1-2 1-3 Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:21:00 AM11:02:00 AM 1:56:00 PM Run Finish Time 10:26:00 AM1:01:00 PM 3:55:00 PM Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Fuel Factor 1.33 1.33 0 Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4258,298.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 5.67 3.48 5.56 4.903 Analyzer Make Thermo Scientific Thermo

Scientific Thermo

Scientific Analyzer Model 48i 48i 48i Analyzer Serial Number CMO8460052CMO846005 2CMO846005

2 Operating Range 99.5 99.5 99.5 99.500 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 11 11 11 11.000 Calibration Pre Zero Cylinder ID Nitrogen-CONitrogen-CONitrogen-CO Calibration Pre Zero Cylinder Instrument Response 0.317 0.317 0.073 0.236 Calibration Pre Zero Cylinder Bias 0.06 0.1 -0.02 0.047 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID BBB00000- CO-MidBBB00000-

CO-MidBBB00000-

CO-Mid Calibration Pre High Cylinder Instrument Response 50.39 50.805 49.658 50.284 Calibration Pre High Cylinder Bias -0.12 0.09 -0.49 -0.173 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-CONitrogen-CONitrogen-CO Calibration Post Zero Cylinder Instrument Response 0.317 0.073 0.048 0.146 Calibration Post Zero Cylinder Bias 0.06 -0.02 -0.04 0.000 Calibration Post Zero Cylinder Drift 0 0.12 0.02 0.047 Calibration Post High Cylinder ID BBB00000- CO-MidBBB00000-

CO-MidBBB00000-

CO-Mid Calibration Post High Cylinder Instrument Response 50.805 49.658 49.755 50.073 Calibration Post High Cylinder Bias 0.09 -0.49 -0.44 -0.280 Calibration Post High Cylinder Drift 0.21 0.58 0.05 0.280 Cavg -0.353 -0.503 -0.528 -0.461 Cavg Units ppmvd ppmvd ppmvd Cgas 0 0 0 0.000 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 38 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 23 Average Run Number 1 2 3 Test Date 7/13/2010 7/14/2010 7/15/2010 Run Start Time 4:15:00 AM5:52:00 AM4:24:00 AM Run Finish Time 8:00:00 PM9:35:00 PM 8:08:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.283 0.283 0.286 0.284 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9971 0.9971 0.9971 0.997 Barometric Pressure, inches of Mercury 29.74 29.825 29.88 29.815 Average Orifice Meter Differential, inches H2O 1.68 1.65 1.80 1.710 Dry Gas Meter Volume Sampled, cubic feet 333.467 327.276 339.742 333.495 Average Dry Gas Meter Temperature, °F 90.98 81.35 88.15 86.827 Dry Gas Meter Volume Sampled, dscf 318.031 318.560 327.311 321.301 Total Moisture Liquid collected, g 429.7 411.4 419.2 420.100 Volume of Water Vapor, standard cubic feet 20.23 19.36 19.73 19.773 Moisture Content of Stack Gas, % 5.98 5.73 5.69 5.800 Moisture Saturation at Stack Gas Temperature, % 81.90 84.08 84.71 83.563 Dry Mole Fraction 0.9402 0.9427 0.9431 0.942 Carbon Dioxide, % 4.368 4.3 4.164 4.277 Oxygen, % 15.051 15.111 15.308 15.157 Carbon Monoxide & Nitrogen, % 80.581 80.589 80.528 80.566 Fuel Factor 1.34 1.35 1.34 Dry Molecular Weight, lb/lb-Mole 29.30 29.29 29.28 29.290 Wet Molecular weight, lb/lb-Mole 28.62 28.64 28.64 28.633 Flue Gas Static Pressure, inches of H2O 0.26 0.25 0.255 0.255 Absolute Flue Gas Pressure, inches of Mercury 29.76 29.84 29.90 29.833 Average Stack Gas Temperature, °F 201.88 203.29 203.75 202.973 Average Velocity Head, inches of H2O 0.3027931239 866490.297985888

6723680.311735218

519044 0.304
Average Stack Gas Velocity, feet/second 34.83 34.53 35.30 34.887 Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703 Dry Volumetric Flow Rate, dry scfm 269,247.0 267,786.6 274,234.8270,422.800 Actual Wet Volumetric Flue Gas Flow Rate, acfm 360,914.7 357,806.1 365,785.0361,501.933 Percent Isokinetic of Sampling Rate, % 97.3 98.0 96.3 97.200 Percent Excess Air, % 241.9 245.1 257.2 248.067 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.833 14.833 14.833 Rectangular Duct Width, inches 157.7 157.7 157.7 Rectangular Duct Length, inches 157.7 157.7 157.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 39 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 25A Average Run Number 1-1 1-2 1-3 Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:21:00 AM11:02:00 AM 1:56:00 PM Run Finish Time 10:26:00 AM1:01:00 PM 3:55:00 PM Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Fuel Factor 1.33 1.33 1.33 Dry Volumetric Flow Rate, dry scfm 273988.82767686000 0 281468.89,225,805,1

52.533 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 5.67 3.48 5.56 4.903 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 51C 51C 51C Analyzer Serial Number 032720220303272022030327202203327,202,203 .000 Operating Range 10 10 10 10.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 911 911 911 911.000 Calibration Pre Zero Cylinder ID Nitrogen-THC NitrogenTHC NitrogenTHC Calibration Pre Zero Cylinder Instrument Response 0.092 0.102 0.012 0.069 Calibration Pre Zero Cylinder Bias 0.4 0.5 -0.4 0.167 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID CCC00000- THC-LowCCC00000-

THC-LowCCC00000-

THC-Low Calibration Pre High Cylinder Instrument Response 3.322 3.234 3.19 3.249 Calibration Pre High Cylinder Bias 2.12 1.24 0.8 1.387 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-THC NitrogenTHC NitrogenTHC Calibration Post Zero Cylinder Instrument Response 0.102 0.012 0.021 0.045 Calibration Post Zero Cylinder Bias 0.5 -0.4 -0.31 -0.070 Calibration Post Zero Cylinder Drift 0.1 0.9 0.09 0.363 Calibration Post High Cylinder ID CCC00000- THC-LowCCC00000-

THC-LowCCC00000-

THC-Low Calibration Post High Cylinder Instrument Response 3.234 3.19 3.281 3.235 Calibration Post High Cylinder Bias 1.24 0.8 1.71 1.250 Calibration Post High Cylinder Drift 0.88 0.44 0.91 0.743 Cavg 0.267 0.24 0.442 0.316 Cavg Units ppmvd ppmvd ppmvd Cgas 0.1603 0.174 0.3966 0.244 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 40 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 26A Average Run Number 1 2 3 Test Date 7/13/2010 7/15/2010 7/15/2010 Run Start Time 5:16:00 PM5:03:00 PM 6:23:00 PM Run Finish Time 6:27:00 PM6:12:00 PM 7:32:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 60 60 60 Nozzle Diameter, inches 0.283 0.286 0.286 0.285 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9971 0.9971 0.9971 0.997 Barometric Pressure, inches of Mercury 29.73 29.875 29.87 29.825 Average Orifice Meter Differential, inches H2O 1.77 1.80 1.83 1.800 Dry Gas Meter Volume Sampled, cubic feet 42.567 42.918 43.290 42.925 Average Dry Gas Meter Temperature, °F 93.71 93.56 96.29 94.520 Dry Gas Meter Volume Sampled, dscf 40.392 40.937 41.085 40.805 Total Moisture Liquid collected, g 81.9 60.6 103.9 82.133 Volume of Water Vapor, standard cubic feet 3.86 2.85 4.89 3.867 Moisture Content of Stack Gas, % 8.72 6.51 10.64 8.623 Moisture Saturation at Stack Gas Temperature, % 85.48 89.36 88.01 87.617 Dry Mole Fraction 0.9128 0.9349 0.8936 0.914 Carbon Dioxide, % 4.4 4.3 4.3 4.333 Oxygen, % 15 15.1 15.1 15.067 Carbon Monoxide & Nitrogen, % 80.6 80.6 80.6 80.600 Fuel Factor 1.34 1.35 1.35 Dry Molecular Weight, lb/lb-Mole 29.30 29.29 29.29 29.293 Wet Molecular weight, lb/lb-Mole 28.31 28.56 28.09 28.320 Flue Gas Static Pressure, inches of H2O -0.29 -0.29 -0.29 -0.290 Absolute Flue Gas Pressure, inches of Mercury 29.71 29.85 29.85 29.803 Average Stack Gas Temperature, °F 203.88 206.29 205.54 205.237 Average Velocity Head, inches of H2O 0.3187229638 037310.311207403

4717070.315416515

150918 0.315
Average Stack Gas Velocity, feet/second 36.02 35.42 35.93 35.790 Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703 Dry Volumetric Flow Rate, dry scfm 269,064.2 271,280.3 263,326.2267,890.233 Actual Wet Volumetric Flue Gas Flow Rate, acfm 373,245.7 367,028.4 372,313.1370,862.400 Percent Isokinetic of Sampling Rate, % 98.9 97.4 100.7 99.000 Percent Excess Air, % 238.9 244.4 244.4 242.567 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.833 14.833 14.833 Rectangular Duct Width, inches 157.7 157.7 157.7 Rectangular Duct Length, inches 157.7 157.7 157.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 41 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 29 Average Run Number 1 2 3 Test Date 7/13/2010 7/14/2010 7/14/2010 Run Start Time 10:39:00 AM7:37:00 AM 2:50:00 PM Run Finish Time 3:59:00 PM12:52:00 PM 8:11:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 300 300 300 Nozzle Diameter, inches 0.283 0.283 0.283 0.283 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9971 0.9971 0.9971 0.997 Barometric Pressure, inches of Mercury 29.58 29.77 29.795 29.715 Average Orifice Meter Differential, inches H2O 1.70 1.73 1.65 1.693 Dry Gas Meter Volume Sampled, cubic feet 206.819 209.429 201.832 206.027 Average Dry Gas Meter Temperature, °F 87.73 88.50 80.73 85.653 Dry Gas Meter Volume Sampled, dscf 197.362 200.864 196.485 198.237 Total Moisture Liquid collected, g 297.9 283.1 264.4 281.800 Volume of Water Vapor, standard cubic feet 14.02 13.33 12.45 13.267 Moisture Content of Stack Gas, % 6.63 6.22 5.96 6.270 Moisture Saturation at Stack Gas Temperature, % 78.30 83.27 80.75 80.773 Dry Mole Fraction 0.9337 0.9378 0.9404 0.937 Carbon Dioxide, % 4.341 4.339 4.315 4.332 Oxygen, % 15.124 15.091 15.072 15.096 Carbon Monoxide & Nitrogen, % 80.535 80.57 80.613 80.573 Fuel Factor 1.33 1.34 1.35 Dry Molecular Weight, lb/lb-Mole 29.30 29.30 29.29 29.297 Wet Molecular weight, lb/lb-Mole 28.55 28.60 28.62 28.590 Flue Gas Static Pressure, inches of H2O -0.29 -0.29 -0.29 -0.290 Absolute Flue Gas Pressure, inches of Mercury 29.56 29.75 29.77 29.693 Average Stack Gas Temperature, °F 199.38 202.67 201.21 201.087 Average Velocity Head, inches of H2O 0.3097998203 235590.315852208

5305730.300525792

208104 0.309
Average Stack Gas Velocity, feet/second 35.33 35.62 34.68 35.210 Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703 Dry Volumetric Flow Rate, dry scfm 270,422.7 274,231.5 268,506.4271,053.533 Actual Wet Volumetric Flue Gas Flow Rate, acfm 366,095.8 369,100.9 359,360.4364,852.367 Percent Isokinetic of Sampling Rate, % 96.2 96.5 96.4 96.367 Percent Excess Air, % 246.4 244.2 242.7 244.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.833 14.833 14.833 Rectangular Duct Width, inches 157.7 157.7 157.7 Rectangular Duct Length, inches 157.7 157.7 157.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 42 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 6C Average Run Number 1-1 1-2 1-3 Test Date 7/15/2010 7/15/2010 7/15/2010 Run Start Time 8:21:00 AM11:02:00 AM 1:56:00 PM Run Finish Time 10:26:00 AM1:01:00 PM 3:55:00 PM Carbon Dioxide, % 4.3 4.2 4.3 4.267 Oxygen, % 15.2 15.3 15.2 15.233 Fuel Factor 1.33 1.33 1.33 Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4258,298.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 5.67 3.48 5.56 4.903 Analyzer Make Ametek Ametek Ametek Analyzer Model 921CD 921CD 921CD Analyzer Serial Number AE-921-6434 AE-921- 6434AE-921-6434
Operating Range 201 201 201 201.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 411 411 411 411.000 Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Pre Zero Cylinder Instrument Response 2.355 4.416 3.729 3.500 Calibration Pre Zero Cylinder Bias 0.27 1.29 0.95 0.837 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID AAL21250- SO2-MidAAL21250-

SO2-MidAAL21250-

SO2-Mid Calibration Pre High Cylinder Instrument Response 108.351 107.321 106.535 107.402 Calibration Pre High Cylinder Bias -1.07 -1.59 -1.98 -1.547 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Post Zero Cylinder Instrument Response 4.416 3.729 3.238 3.794 Calibration Post Zero Cylinder Bias 1.29 0.95 0.71 0.983 Calibration Post Zero Cylinder Drift 1.02 0.34 0.24 0.533 Calibration Post High Cylinder ID AAL21250- SO2-MidAAL21250-

SO2-MidAAL21250-

SO2-Mid Calibration Post High Cylinder Instrument Response 107.321 106.535 106.634 106.830 Calibration Post High Cylinder Bias -1.59 -1.98 -1.93 -1.833 Calibration Post High Cylinder Drift 0.52 0.39 0.05 0.320 Cavg 48.495 47.872 47.986 48.118 Cavg Units ppmvd ppmvd ppmvd Cgas 47.1607 46.5012 47.1351 46.932 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 43 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 6C 3 Average Run Number 3-1 3-2 3-3 Test Date 7/13/2010 7/15/2010 7/15/2010 Run Start Time 5:18:00 PM5:04:00 PM 6:23:00 PM Run Finish Time 6:24:00 PM6:03:00 PM 7:22:00 PM Carbon Dioxide, % 4.4 4.3 4.3 4.333 Oxygen, % 15 15.1 15.1 15.067 Fuel Factor 0 1.35 1.35 Dry Volumetric Flow Rate, dry scfm 252456.3 245857.5 238787.9245,700.567 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 4.83 6.51 10.64 7.327 Analyzer Make Ametek Ametek Ametek Analyzer Model 921CE 921CE 921CE Analyzer Serial Number AE-921-6434 AD-921- 6434AE-921-6434
Operating Range 201 201 201 201.000 Operating Units ppm ppm ppm No. Readings/Avg. 60 60 60 60.000 Calibration Set 611 412 412 478.333 Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Pre Zero Cylinder Instrument Response 1.995 3.238 2.935 2.723 Calibration Pre Zero Cylinder Bias 0 0.71 0.56 0.423 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID ALM045659- SO2-MidAAL21250-

SO2-MidAAL21250-

SO2-Mid Calibration Pre High Cylinder Instrument Response 97.332 106.634 106.32 103.429 Calibration Pre High Cylinder Bias -2.07 -1.93 -2.08 -2.027 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Post Zero Cylinder Instrument Response 2.888 2.935 3.238 3.020 Calibration Post Zero Cylinder Bias 0.45 0.56 0.71 0.573 Calibration Post Zero Cylinder Drift 0.45 0.15 0.15 0.250 Calibration Post High Cylinder ID ALM045659- SO2-MidAAL21250-

SO2-MidAAL21250-

SO2-Mid Calibration Post High Cylinder Instrument Response 96.969 106.32 106.634 103.308 Calibration Post High Cylinder Bias -2.25 -2.08 -1.93 -2.087 Calibration Post High Cylinder Drift 0.18 0.15 0.15 0.160 Cavg 47.958 47.773 47.943 47.891 Cavg Units ppmvd ppmvd ppmvd Cgas 47.5787 47.1974 47.377 47.384 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 44 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - Method 7E Average Run Number 3-1 3-2 3-3 Test Date 7/13/2010 7/15/2010 7/15/2010 Run Start Time 5:18:00 PM5:04:00 PM 6:23:00 PM Run Finish Time 6:24:00 PM6:03:00 PM 7:22:00 PM Carbon Dioxide, % 4.4 4.3 4.3 4.333 Oxygen, % 15 15.1 15.1 15.067 Fuel Factor 1.34 1.35 1.35 Dry Volumetric Flow Rate, dry scfm 253680.3 260826.6 260388.4258,298.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 5.67 3.48 5.56 4.903 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 42CLS 42CLS 42CLS Analyzer Serial Number 032820242703282024270328202427328,202,427 .000 Operating Range 201 201 201 201.000 Operating Units ppm PPM ppm No. Readings/Avg. 60 60 60 60.000 Calibration Set 112 111 111 111.333 Calibration Pre Zero Cylinder ID Nitrogen-NOx NitrogenNOx NitrogenNOx Calibration Pre Zero Cylinder Instrument Response 0.322 0.329 0.422 0.358 Calibration Pre Zero Cylinder Bias 0.21 0 0.04 0.083 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID ALM045659- NOx-MidAAL21250-

NOx-MidAAL21250-

NOx-Mid Calibration Pre High Cylinder Instrument Response 100.2 107.835 107.911 105.315 Calibration Pre High Cylinder Bias -0.93 -0.84 -0.8 -0.857 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-NOx NitrogenNOx NitrogenNOx Calibration Post Zero Cylinder Instrument Response 0.392 0.422 0.411 0.408 Calibration Post Zero Cylinder Bias 0.24 0.04 0.25 0.177 Calibration Post Zero Cylinder Drift 0.03 0.04 1.9 0.657 Calibration Post High Cylinder ID ALM045659- NOx-MidAAL21250-

NOx-MidAAL21250-

NOx-Mid Calibration Post High Cylinder Instrument Response 99.42 107.911 106.333 104.555 Calibration Post High Cylinder Bias -1.32 -0.8 -1.59 -1.237 Calibration Post High Cylinder Drift 0.393.999999999 99999E-02 0.79 0.407
Cavg 60.528 63.039 63.761 62.443 Cavg Units ppmvd ppmvd ppmvd Cgas 60.0179 64.5886 65.7752 63.461 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 45 of 46

### PSEG Sewaren Unit 1
9/30/2010
LocationStack Exit - OTM - 27/28 Average Run Number 1 2 3 Test Date 7/13/2010 7/14/2010 7/14/2010 Run Start Time 10:39:00 AM7:37:00 AM 2:50:00 PM Run Finish Time 4:40:00 PM1:21:00 PM 8:37:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 335.42 330.1 330.63 Nozzle Diameter, inches 0.207 0.207 0.207 0.207 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988 Barometric Pressure, inches of Mercury 29.575 29.77 29.78 29.708 Average Orifice Meter Differential, inches H2O 0.45 0.45 0.45 0.450 Dry Gas Meter Volume Sampled, cubic feet 136.658 130.761 134.692 134.037 Average Dry Gas Meter Temperature, °F 88.58 90.75 86.58 88.637 Dry Gas Meter Volume Sampled, dscf 128.624 123.396 128.119 126.713 Total Moisture Liquid collected, g 188.8 168.2 176 177.667 Volume of Water Vapor, standard cubic feet 8.89 7.92 8.28 8.363 Moisture Content of Stack Gas, % 6.46 6.03 6.07 6.187 Moisture Saturation at Stack Gas Temperature, % 96.80 94.08 100.00 96.960 Dry Mole Fraction 0.9354 0.9397 0.9393 0.938 Carbon Dioxide, % 4.341 4.339 4.315 4.332 Oxygen, % 15.124 15.091 15.072 15.096 Carbon Monoxide & Nitrogen, % 80.535 80.57 80.613 80.573 Fuel Factor 1.33 1.34 1.35 Dry Molecular Weight, lb/lb-Mole 29.30 29.30 29.29 29.297 Wet Molecular weight, lb/lb-Mole 28.57 28.62 28.60 28.597 Flue Gas Static Pressure, inches of H2O -0.29 -0.29 0.29 -0.097 Absolute Flue Gas Pressure, inches of Mercury 29.55 29.75 29.80 29.700 Average Stack Gas Temperature, °F 209.75 208.67 214.25 210.890 Average Velocity Head, inches of H2O 0.3210645728 285740.293201106

6337570.311593043

91876 0.309
Average Stack Gas Velocity, feet/second 36.24 34.46 35.65 35.450 Stack Cross-Sectional Area, square feet 172.703 172.703 172.703 172.703 Dry Volumetric Flow Rate, dry scfm 273,497.8 263,453.0 270,634.2269,195.000 Actual Wet Volumetric Flue Gas Flow Rate, acfm 375,525.4 357,080.7 369,411.7367,339.267 Percent Isokinetic of Sampling Rate, % 103.6 104.9 105.8 104.767 Percent Excess Air, % 246.4 244.2 242.7 244.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.833 14.833 14.833 Rectangular Duct Width, inches 157.7 157.7 157.7 Rectangular Duct Length, inches 157.7 157.7 157.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 46 of 46