NREL is a national laboratory of the U.S. Department of Energy

Office of Energy Efficiency & Renewable Energy

Operated by the Alliance for Sustainable Energy, LLC

This report is available at no cost from the National Renewable Energy

Laboratory (NREL) at www.nrel.gov/publications.

Contract No. DE-AC36-8GO28308

National Renewable Energy Laboratory

15013 Denver West Parkway

Golden, CO 80401

303-275-3000 • www.nrel.gov

Residential Energy Efficiency

Demonstration

Hawaii and Guam Energy 

Improvement Technology 

Demonstration Project

L. Earle and B. Sparn

National Renewable Energy Laboratory

A. Rutter

Guam Sustainability Solutions LLC

D. Briggs

Naval Base Guam

Produced under direction of Naval Facilities Engineering 

Command (NAVFAC) by the National Renewable Energy 

Laboratory (NREL) under Interagency Agreement 11-01829

Technical Report

NREL/TP-5500-61013

March 2014
NREL is a national laboratory of the U.S. Department of Energy

Office of Energy Efficiency & Renewable Energy

Operated by the Alliance for Sustainable Energy, LLC

This report is available at no cost from the National Renewable Energy

Laboratory (NREL) at www.nrel.gov/publications.

Contract No. DE-AC36-8GO28308

National Renewable Energy Laboratory

15013 Denver West Parkway

Golden, CO 80401

303-275-3000 • www.nrel.gov

Residential Energy Efficiency

Demonstration

Hawaii and Guam Energy 

Improvement Technology 

Demonstration Project

L. Earle and B. Sparn

National Renewable Energy Laboratory

A. Rutter

Guam Sustainability Solutions LLC

D. Briggs

Naval Base Guam

Technical Report

NREL/TP-5500-61013

March 2014
NOTICE

This manuscript has been authored by employees of the Alliance for Sustainable Energy, LLC (“Alliance”) under 

Contract No. DE-AC36-08GO28308 with the U.S. Department of Energy (“DOE”).

This report was prepared as an account of work sponsored by an agency of the United States government. 

Neither the United States government nor any agency thereof, nor any of their employees, makes any warranty, 

express or implied, or assumes any legal liability or responsibility for the accuracy, completeness, or usefulness of 

any information, apparatus, product, or process disclosed, or represents that its use would not infringe privately 

owned rights. Reference herein to any specific commercial product, process, or service by trade name, 

trademark, manufacturer, or otherwise does not necessarily constitute or imply its endorsement, recommendation, 

or favoring by the United States government or any agency thereof. The views and opinions of authors expressed 

herein do not necessarily state or reflect those of the United States government or any agency thereof.

Printed on paper containing at least 50% wastepaper, including 10% post consumer waste.
iii

Acknowledgments 

The authors wish to acknowledge the staff at Naval Base Guam for hosting this demonstration and 

providing key support from initial design to project completion. We thank Elaine Cruz, Justin Eustaquio, 

Ray Garrido, Marlyna Gumabon, Glen Primero, and Edwin Rengiil of Naval Base Guam Housing, and 

Navy Lieutenant Asher Goldenberg. 

The project could not have met success without the coordination and oversight from Naval Facilities 

Engineering Command (NAVFAC), and we thank Florence Ching, Kenneth Estores, and Morris Ishida of 

NAVFAC Pacific and Kevin Hurley of NAVFAC Headquarters. 

The demonstration was made possible because of the generous cooperation of the residents whose homes 

were used for the appliance upgrades and advanced power strip installations. We thank them for allowing 

us into their homes to install various equipment and for their patience when repeated visits were necessary 

to troubleshoot our data acquisition system. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
iv

List of Abbreviations and Acronyms

A/C air conditioning 

AHU air handler unit 

AIRR adjusted internal rate of return

APS advanced power strip

ASHRAE American Society of Heating, Refrigerating and Air Conditioning Engineers 

BEopt Building Energy Optimization

BEoptE+ Building Energy Optimization with EnergyPlus

BLCC Building Life-Cycle Cost

CT current transformer

DHW domestic hot water

DOD U.S. Department of Defense

EEE enhanced energy efficiency

eROI energy return on investment 

FY fiscal year

HPWH heat pump water heater 

HVAC heating, ventilation, and air conditioning 

IR infrared

JRM Joint Region Marianas

kWh kilowatt-hour 

MWh megawatt-hour 

NAVFAC Naval Facilities Engineering Command

NBG Naval Base Guam

NEEP Northeast Energy Efficiency Partnerships 

NEPA National Environmental Policy Act

NIST National Institute of Standards and Technology 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
v 

NOAA National Oceanic and Atmospheric Administration

NREL National Renewable Energy Laboratory 

T&RH temperature and relative humidity

TRL technology readiness level

SEER seasonal energy efficiency ratio

SFH single-family home 

SIR savings-to-investment ratio

W watt

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
vi 

Executive Summary

In order to meet its energy goals, the U.S. Department of Defense has partnered with the U.S. Department 

of Energy’s National Renewable Energy Laboratory (NREL) to rapidly demonstrate and deploy costeffective renewable energy and energy efficiency technologies. The scope of this project was to 

demonstrate tools and technologies to reduce energy use in military housing, with particular emphasis on 

measuring and reducing loads related to consumer electronics (commonly referred to as “plug loads”), hot 

water, and whole-house cooling. 

A plug load-reducing technology called the advanced power strip (APS) was installed in homes and 

monitored for energy savings, and the residents were trained in the use of these new devices. For hot 

water and cooling, building energy simulation tools were used to select the enhanced energy efficiency 

(EEE) package of cost-effective retrofit technologies. The technologies installed in these homes included 

high-efficiency air conditioners and air handlers, in-line dehumidifiers (in a subset of homes), internetconnected programmable thermostats, low-flow shower heads, and heat pump water heaters. The impact 

on energy use of the space-conditioning and hot water system upgrades was measured to determine 

annual energy savings. The design of the EEE demonstration was facilitated by Building Energy 

Optimization (BEopt), an optimization software developed at NREL. 

Overall, the APS and EEE demonstrations both saved energy, although house-to-house variations in 

achieved savings were large. The results from the APS demonstration indicate expected annual energy 

savings of 58 kilowatt-hours (kWh) in a home entertainment center and 40 kWh in a home office. The 

APS demonstration is projected to save $600 total for 30 homes over the next four years. Economic 

results of the APS demonstration were not positive, indicating deployment of this technology in a military 

housing environment may not yield appreciable savings without further study to evaluate effective options 

to implementation. The EEE demonstration resulted in much higher annual energy savings, with an 

average of 4,000 kWh in heating, ventilation, and air conditioning energy savings and 1,400 kWh in 

domestic hot water savings. These savings translate to substantial cost savings in Guam, where electricity 

costs 50¢/kWh. The EEE demonstration is projected to result in a net savings (after paying for the initial 

investment in the first three years) of $120,000 over the next 10 years for all eight homes, or an average of 

$15,000 per home over 10 years.

All of the products evaluated in this demonstration are commercially available and can be purchased from 

a variety of companies and retailers. A number of different strategies could be used to increase the use of 

APSs in base housing, including stocking APSs in the base Naval Exchange, distributing APSs to all new 

families during move-ins, or employing a direct installation program. The EEE technologies have already 

been integrated into the standards for new equipment for new and existing homes on Naval Base Guam. 

The residential energy-efficiency equipment evaluated in this demonstration is projected to save energy 

and money while maintaining or improving indoor comfort, and thus, are a good investment for the U.S. 

Navy. APSs are a simple, low-cost way to reduce plug load consumption, but it may be a challenge to 

ensure they are installed properly. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
vii 

Table of Contents

Acknowledgments ..................................................................................................................................... iii

List of Abbreviations and Acronyms ....................................................................................................... iv

Executive Summary................................................................................................................................... vi

List of Figures ............................................................................................................................................ ix

List of Tables............................................................................................................................................... x

1 Introduction........................................................................................................................................... 1

1.1 Background ................................................................................................................................... 1

2 Demonstration Objective ..................................................................................................................... 3

2.1 Technology Description ................................................................................................................ 3

2.1.1 Residential Plug Load-Reduction Technologies ............................................................... 3

2.1.2 Water Heating and Cooling Load Reduction Technologies ............................................. 5

3 Demonstration Design ......................................................................................................................... 7

3.1 Demonstration Design and Simulation ......................................................................................... 7

3.1.1 Advanced Power Strip Demonstration Design ................................................................. 7

3.1.2 Enhanced Energy Efficiency Demonstration Design........................................................ 7

3.2 Facility/Site Description................................................................................................................ 9

3.2.1 Advanced Power Strip Demonstration Sites ..................................................................... 9

3.2.2 Enhanced Energy Efficiency Demonstration Sites ......................................................... 11

3.3 Monitoring Equipment and Installation ...................................................................................... 13

3.3.1 Advanced Power Strip Demonstration Monitoring Equipment ...................................... 13

3.3.2 Enhanced Energy Efficiency Demonstration Monitoring Equipment ............................ 15

3.4 Baseline Characterization ............................................................................................................ 19

3.4.1 Advanced Power Strip Demonstration Baseline Testing ................................................ 19

3.4.2 Enhanced Energy Efficiency Demonstration Baseline Testing ...................................... 19

3.5 Demonstration Period.................................................................................................................. 20

3.5.1 Advanced Power Strip Demonstration............................................................................ 20

3.5.2 Enhanced Energy Efficiency Demonstration .................................................................. 20

3.6 Summary of Performance Objectives ......................................................................................... 21

3.7 Pre- and Post-Demonstration Surveys......................................................................................... 21

4 Technical Performance Analysis and Assessment ........................................................................ 22

4.1 Overview ..................................................................................................................................... 22

4.1.1 Overview of Technical Performance for Advanced Power Strip Demonstration ........... 22

4.1.2 Overview of Technical Performance for Enhanced Energy Efficiency Demonstration . 22

4.2 Results ......................................................................................................................................... 22

4.2.1 Advanced Power Strip Demonstration Results ............................................................... 22

4.2.2 Enhanced Energy Efficiency Demonstration Results ..................................................... 25

4.3 Energy Model Simulations .......................................................................................................... 31

4.3.1 Annual Energy Use Simulation for Advanced Power Strip Homes ............................... 31

4.3.2 Annual Energy Use Simulation for Enhanced Energy Efficiency Homes ...................... 31

4.4 Analysis of Results ...................................................................................................................... 35

4.4.1 Advanced Power Strip Demonstration Results Analysis ................................................ 35

4.4.2 Enhanced Energy Efficiency Demonstration Results Analysis ...................................... 38

4.5 User Feedback and Survey Results ............................................................................................. 39

4.5.1 Advanced Power Strip User Feedback ........................................................................... 39

4.5.2 Enhanced Energy Efficiency User Feedback .................................................................. 39

4.6 Assessment of Performance Objectives ...................................................................................... 41

5 Economic Performance Analysis and Assessment........................................................................ 42

5.1 Economic Performance of Advanced Power Strip Demonstration ............................................. 42

5.2 Economic Performance of Enhanced Energy Efficiency Demonstration ................................... 42

6 Project Management Considerations ............................................................................................... 46

6.1 Site Approval, National Environmental Policy Act, and DD1391.............................................. 47

6.1.1 Advanced Power Strip Demonstration............................................................................ 47

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
viii

6.1.2 Enhanced Energy Efficiency Demonstration .................................................................. 47

6.2 Contracts and Procurement ......................................................................................................... 48

6.3 Design ......................................................................................................................................... 48

6.4 Installation and Construction ...................................................................................................... 48

6.5 Operation and Maintenance ........................................................................................................ 48

6.6 Training ....................................................................................................................................... 49

7 Commercial Readiness Qualitative Assessment ............................................................................ 50

7.1 Commercial Readiness of Advanced Power Strips ..................................................................... 50

7.2 Commercial Readiness of Enhanced Energy Efficiency Technologies ...................................... 50

8 Recommended Next Steps ................................................................................................................ 52

8.1 Recommended Next Steps for Advanced Power Strips .............................................................. 52

8.2 Recommended Next Steps for Enhanced Energy Efficiency Technologies ............................... 52

References................................................................................................................................................. 54

Appendix A: Advanced Power Strip Fact Sheet .................................................................................... 55

Appendix B: Advanced Power Strip Installation Instructions.............................................................. 56

Appendix C: Advanced Power Strip Pre- and Post-Demonstration Surveys ..................................... 58

Advanced Power Strips: Pre-Demonstration Questions ....................................................................... 58

Advanced Power Strips: Post-Demonstration Questions ..................................................................... 59

Appendix D: Enhanced Energy Efficiency Post-Demonstration Survey ............................................ 60

Enhanced Energy Efficiency: Post Demonstration Questions ............................................................. 60

Appendix E: Economic Analysis for Advanced Power Strip and Enhanced Energy Efficiency 

Demonstrations .................................................................................................................................. 61

Cost Information .................................................................................................................................. 61

Cost Assumptions for Minimally Efficient Retrofit .................................................................... 61

Economic Analysis Information ........................................................................................................... 61

Energy Return on Investment Analyses ...................................................................................... 61

Building Life-Cycle Cost Analyses ............................................................................................ 63

Appendix F: Consumer Guide for Advanced Power Strips.................................................................. 64

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
ix

List of Figures

Figure 1. Embertec Emberceptor AV APS for entertainment centers .......................................................... 4

Figure 2. Belkin Conserve APS for home offices ......................................................................................... 4

Figure 3. A.O. Smith Voltex 60-gallon HPWH ............................................................................................ 5

Figure 4. Lennox XC21 A/C......................................................................................................................... 5

Figure 5. Lennox CBX32MV variable speed, multi-position air handler .................................................... 5

Figure 6. Lennox Humiditrol whole-house dehumidification system .......................................................... 6

Figure 7. Lennox iComfort Wi-Fi thermostat ............................................................................................... 6

Figure 8. American Standard 1660.717.002 FloWise three-function showerhead ....................................... 6

Figure 9. BEopt optimization curve for one of the EEE homes ................................................................... 8

Figure 10. Simulated annual energy consumption by end use for pre- and post-retrofit house.................... 8

Figure 11. Typical residence in Lockwood Terrace neighborhood on NBG .............................................. 12

Figure 12. One side of a duplex in the North Tipalao neighborhood on NBG ........................................... 12

Figure 13. Map of EEE demonstration sites ............................................................................................... 13

Figure 14. A Watt'sUp.net meter setup ....................................................................................................... 14

Figure 15. An eMonitor meter installed in an EEE home with two breaker panels ................................... 16

Figure 16. A flow meter and HOBO state logger at the water heater ......................................................... 16

Figure 17. A T&RH sensor next to the thermostat in an EEE home .......................................................... 17

Figure 18. Daily hot water energy consumption for Lockwood 1 .............................................................. 27

Figure 19. Daily hot water energy consumption for Tipalao 3 ................................................................... 27

Figure 20. Daily HVAC energy consumption for Lockwood 1 .................................................................. 28

Figure 21. Daily HVAC energy consumption for Tipalao 3 ...................................................................... 28

Figure 22. Daily household energy use for Lockwood 1 ............................................................................ 29

Figure 23. Daily household energy use for Tipalao 3 ................................................................................. 29

Figure 24. BEopt model for a Lockwood Terrace home ............................................................................ 31

Figure 25. BEopt model for a North Tipalao home (half a duplex shown) ................................................ 31

Figure 26. Outdoor temperature and humidity over the past year in Guam ............................................... 32

Figure 27. Measured vs. modeled HVAC mean daily energy use .............................................................. 33

Figure 28. Measured vs. modeled DHW mean daily energy use ................................................................ 34

Figure 29. Home entertainment center power consumption in House G before and after APS ................. 36

Figure 30. Histogram of entertainment center daily energy use in House G before and after APS ........... 36

Figure 31. Home entertainment center power consumption in House A before and after APS ................. 37

Figure 32. Histogram of entertainment center daily energy use in House A before and after APS ........... 38

Figure 33. Annual HVAC and DHW savings per house ............................................................................ 45

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
x 

List of Tables

Table 1. APS Demonstration Participants .................................................................................................. 10

Table 2. EEE Demonstration Participants .................................................................................................. 12

Table 3. Data Collection Details for APS Demonstration .......................................................................... 14

Table 4. Data Collection Details for EEE Demonstration .......................................................................... 18

Table 5. Performance Objectives ................................................................................................................ 21

Table 6. Summary of APS Installations ...................................................................................................... 23

Table 7. Mean Daily Energy Consumptions for Home Entertainment Center Installations ....................... 24

Table 8. Mean Daily Energy Consumption for Home Office Installations ................................................ 25

Table 9. Summary of Mean Daily Energy Use for DHW Systems in EEE Homes .................................... 25

Table 10. Summary of Mean Daily Energy Use for HVAC Systems in EEE Homes ................................ 26

Table 11. Summary of Mean Daily Whole House Energy Use for EEE Homes ........................................ 26

Table 12. Indoor Conditions Before and After the Retrofit for all EEE Homes ......................................... 30

Table 13. Summary of Hot Water Usage per House .................................................................................. 30

Table 14. Annual Simulation Results ......................................................................................................... 35

Table 15. Annual Energy Savings from APS ............................................................................................. 35

Table 16. Assessment of Performance Objectives ...................................................................................... 41

Table 17. Economic Analysis of APS Demonstration ................................................................................ 42

Table 18. Overall Economic Analysis of EEE Demonstration ................................................................... 43

Table 19. Economic Analysis of EEE Demonstration on a per Unit Basis ................................................ 44

Table 20. Summary of Programmatic Elements for APS and EEE Demonstrations .................................. 46

Table A-1. Estimated, Unburdened Equipment Pricing for the Minimally Efficient Retrofits .................. 61

Table A-2. Key Information Regarding eROI Analyses Performed for this Report .................................. 62

Table A-3. Key Information Regarding BLCC Analyses Performed for this Report ................................. 63

Table A-4. Key Information Regarding BLCC Analyses Performed for this Report ................................. 63

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
1 

1 Introduction

In order to meet its energy goals, the U.S. Department of Defense (DOD) has partnered with the U.S. 

Department of Energy’s National Renewable Energy Laboratory (NREL) to rapidly demonstrate and 

deploy cost-effective renewable energy and energy efficiency technologies. The common goal is to

demonstrate and measure the performance and economic benefit of the system while monitoring any 

ancillary impacts to related standards of service and operation and maintenance practices. The standards 

of service may include acceptable temperature and humidity ranges, power quality, allowable setbacks, 

noise criteria, air quality parameters, lighting levels, and other related factors. In short, demonstrations at 

DOD facilities simultaneously evaluate the benefits and compatibility of the technology with the DOD 

mission, and with its design, construction, and operation and maintenance practices, in particular.

This report discusses one of several demonstrations of new or underutilized commercial energy 

technologies. 

1.1 Background

The scope of this project was to demonstrate tools and technologies to reduce energy use in military 

housing, with particular emphasis on measuring and reducing loads related to consumer electronics 

(commonly referred to as “plug loads”), hot water, and whole-house cooling. Plug load-reducing 

technologies were installed and monitored for energy savings, and the tenants were trained in the use of 

these new devices. For hot water and cooling, building energy simulation tools were used to select costeffective retrofit technologies. The results were compared to the simulation tool’s predicted outcomes to 

validate the use of the tool in the retrofit selection process. The impact on energy use of the spaceconditioning and hot water system upgrades was measured to determine annual energy savings. 

The demonstration was organized in two tiers. As little is known about the magnitude of plug load energy 

use and the potential to reduce it in military housing, residential plug load measurement and reduction 

were the focus of the first part of this demonstration. Through the demonstration, NREL measured and 

provided user-friendly control over the energy consumption of consumer electronics used in the home 

entertainment center (TV and peripherals) and the home office (computer and peripherals) areas. In 

addition to the common problem of users neglecting to turn off unused appliances, plug loads waste 

energy in the form of “vampire” or “phantom” loads—many devices continue to draw current as long as 

they remain plugged into receptacles, even after the appliances are switched off. The emerging technology 

class of products called the advanced power strip (APS) seeks to address the growing plug load energy 

waste via auto-switching capabilities, where supply power is automatically shut off when the end-use 

appliance is detected to be in an unused state. In this project, APS devices were installed on all home 

office and entertainment center areas in 30 Naval Base Guam (NBG) houses, and the electrical outlets 

were monitored for changes in energy use. Throughout this report, the authors refer to this component of 

the project as the “APS demonstration.” 

The second part, which is called the “enhanced energy efficiency (EEE) demonstration,” is a more 

comprehensive upgrade package designed to cost-effectively reduce energy consumption of the largest 

loads in these homes. Using basic information on floor plan and building construction, energy models 

were developed using Building Energy Optimization (BEopt) with EnergyPlus1 for several typical houses 

on NBG (Christensen, Anderson, Horowitz, Courtney, & Spencer, 2006). Using these models, NREL 

 

1 BEopt with EnergyPlus (BEoptE+) version 2.0.0.6 was used for this project. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
2 

determined the most effective strategy to reducing energy consumption in these concrete, all-electric 

homes is to reduce the heating, ventilation, and air conditioning (HVAC) and domestic hot water (DHW) 

loads. The best way to decrease HVAC-related energy use is to improve the efficiency of the equipment, 

and if occupancy schedules allow, employ thermostat setups. Improving supplemental dehumidification 

could improve comfort, substantially decrease the sensible cooling requirements, and increase the 

durability of the homes by reducing moisture, which can contribute to mold growth and related health 

concerns. Heat pump water heaters (HPWH) are an excellent alternative to electric resistance water 

heaters, especially in a consistently hot and humid climate such as Guam's. NREL demonstrated the 

energy-saving potential of these technologies in eight NBG houses so that they may be considered in 

future equipment replacement, as well as new construction.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
3 

2 Demonstration Objective

The objective of this project was to demonstrate several cost-effective measures that can be easily 

implemented in U.S. Navy base housing to reduce whole-house energy consumption, with particular 

focus on residential plug loads, water heating loads, and cooling loads. Energy monitoring was conducted 

before and after the upgrades were deployed to measure resulting changes in energy use. 

Military housing poses several unique challenges to energy reduction strategies. Base housing may not be 

individually metered, and utility bills might not be paid by the homes' occupants, resulting in no direct 

feedback on electricity use and no monetary incentive to reduce it. It may be common for military 

families to have someone at home during the day, so strategies that rely on reducing consumption when 

the home is empty (e.g., air-conditioning setback, whole-house green switch) may not be effective for all 

families. The simplest plug load reduction program for military housing would target small appliances 

and electronics because occupants have direct control of these end uses. 

In addition, the tropical climate of Guam makes the cooling and dehumidification requirements a 

dominant source of electricity use. Improving the efficiency of the HVAC equipment and replacing major 

appliances, such as the water heater, with energy efficient models will dramatically reduce the energy use 

of base housing while maintaining occupant comfort. 

2.1 Technology Description

2.1.1 Residential Plug Load-Reduction Technologies

Advanced Power Strips 

APS products come with a variety of control mechanisms ranging in degree of automation and can 

provide the appropriate balance of intelligent control and convenience to reduce plug load waste while 

minimizing required changes in occupant behavior. Currently available APS devices are primarily 

designed for use in home entertainment centers and home offices, where the concentration of consumer 

electronics is typically high, and the controls rely on sensing the power state of the designated “master” 

appliance (usually the TV or computer). Power to peripheral equipment (e.g., DVD player, game console, 

printer) is turned off when the master device is turned off or in standby mode. 

Two different APS products were used in this demonstration: one for the home entertainment area and 

another for the home office. Both rely on current sensing for control, but the APS for the home 

entertainment center has one additional layer of control. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
4 

Figure 1. Embertec Emberceptor AV APS for entertainment centers

The Embertec Emberceptor AV, shown in Figure 1, was used in the home entertainment centers. This is a 

current-sensing APS that uses an infrared (IR) sensor for additional control. Power to the green 

“controlled” outlets is shut off if all the connected devices are turned off (i.e., the current draw is very 

low). The controlled outlets are turned back on when the IR sensor detects the use of a remote control (the 

IR sensor does not detect occupant movement). A timer function exists that turns off the controlled outlets 

if there has not been any remote control activity for three hours. This feature can be useful in homes 

where the television is often left on inadvertently. The remote control activity is used as a proxy to 

indicate someone is actively using the television. Before the outlets are turned off with the timer function, 

a green indicator light flashes to warn the user. If there is no remote control activity, it is assumed the user 

has left the room or fallen asleep. This timer function can be turned off if desired. There are also three 

“always on” outlets available for devices that need to remain powered on at all times, such as a cable box. 

Figure 2. Belkin Conserve APS for home offices

The Belkin Conserve, shown in Figure 2, was used in the home office areas. This device has a typical 

master-controlled algorithm, where the computer is plugged into the “master” outlet and all related 

electronics are plugged into the controlled outlets. The controlled outlets are completely turned off when 

the computer is off or asleep. There are also two “always on” outlets for devices that need to remain 

powered on at all times, such as a wireless router. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
5 

2.1.2 Water Heating and Cooling Load Reduction Technologies

Heat Pump Water Heater

An HPWH pulls heat from the surrounding air and uses it to heat the water in a storage tank. The newest 

generation of this equipment is an integrated system with a built-in storage tank. Because heat is extracted 

from the air rather than generated directly, an HPWH offers significant energy savings over a 

conventional electric resistance water heater. This technology is ideally suited to Guam's hot, humid 

climate, and is a particularly attractive alternative where gas heating is not available, electricity prices are 

high, and typhoon-resistant solar water heating installation can be expensive. An HPWH can usually be 

installed as a direct replacement to the existing storage tank water heater without additional changes to the 

plumbing or surroundings, provided that sufficient space requirements are met. See Figure 3. 

Figure 3. A.O. Smith Voltex 60-gallon HPWH

SEER 21 Air Conditioner and Variable-Speed Air Handler

Replacing the existing air conditioning (A/C) system with a newer, higher efficiency-rated system 

significantly decreases energy required to cool the house. See Figure 4 and Figure 5. 

Figure 4. Lennox XC21 A/C

Figure 5. Lennox CBX32MV variable speed, multi-position air handler

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
6 

Air Conditioner-Integrated Whole-Home Dehumidification System

In three of the eight homes, the standalone dehumidifier was replaced with a whole-home 

dehumidification system that features advanced control logic designed to integrate with the new A/C 

system to maintain optimal indoor humidity. The dehumidifier is located in the same closet as, and 

positioned in series with, the air handler unit (AHU). See Figure 6. 

Figure 6. Lennox Humiditrol whole-house dehumidification system

Programmable Thermostat

The existing thermostat was replaced with a programmable thermostat that allows residents to set a 

schedule that works for them, such as a daytime setup. Modest increases in thermostat set points during 

unoccupied hours can result in substantial reduction in HVAC-related energy consumption. The 

thermostat is also a humidistat that is needed for control in the homes with the new whole-home 

dehumidifier. See Figure 7. 

Figure 7. Lennox iComfort Wi-Fi thermostat

Low-Flow Shower Head

All existing shower heads were replaced with low-flow shower heads to reduce hot water consumption. 

See Figure 8. 

Figure 8. American Standard 1660.717.002 FloWise three-function showerhead

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
7 

3 Demonstration Design

This demonstration was designed as two parts due the relative magnitude of expected savings. Larger 

savings were expected from improving A/C and DHW efficiency so fewer homes were needed. APSs 

have much smaller expected savings so a larger sample size was needed for statistical purposes. Both 

parts of the demonstration included a base load monitoring period before efficiency measures were

installed. In addition to energy consumption of the appliances of interest, temperature and relative 

humidity data were collected for the EEE demonstration at five locations in each home (four in the house 

and one by the HPWH), along with hot water consumption data. These data continued to be collected 

after the efficiency upgrades were installed. In APS homes, energy consumption of plug load areas were

collected (e.g., home entertainment area, home office) before and after APS installation.

The overall schedule for both parts of this demonstration was as follows: first, monitoring equipment was 

installed in the homes to provide base load data from before the retrofits. Equipment upgrades were then 

implemented, and the post-retrofit energy use was monitored for several months afterward. Data 

collection occurred throughout the baseline and demonstration periods. The data were analyzed at the end

of the study period when the monitoring equipment was removed. All efficiency upgrades remained in 

place after the conclusion of the demonstration. 

3.1 Demonstration Design and Simulation

The two demonstrations were designed using a combination of past laboratory tests and simulation 

studies.

3.1.1 Advanced Power Strip Demonstration Design

The APS demonstration specifically targeted reducing plug loads in residential buildings, which are 

primarily concentrated in the home office and home entertainment center. APSs, which are designed 

specifically for use with consumer electronics in these areas, are commercially available and underutilized 

so this demonstration presented an opportunity to measure their efficacy in real home scenarios. 

The choice of APSs deployed in this demonstration was based on laboratory tests performed at NREL in 

2012 (Earle & Sparn, 2012). The laboratory tests were focused on assessing how effective the APSs are 

and how much they impact a user's normal operation of the connected electronics. The two APSs chosen

for the demonstration (the Emberceptor AV and the Conserve) scored high in effectiveness and usability. 

The Emberceptor AV is a masterless APS with a unique feature that monitors remote control activity in 

the entertainment center and shuts off the controlled electronics if it detects they are no longer being used 

(either because the user has fallen asleep or left the room). The Conserve is a master-controlled APS with 

an auto-adjusting threshold, which works well in home office environments. 

3.1.2 Enhanced Energy Efficiency Demonstration Design

Guam is a tropical island with year-round cooling and dehumidifying loads, which make up a large 

fraction of the energy used in residential buildings there. While the home’s envelope plays a large role in 

the space-conditioning needs of the house, it was not feasible in this project to improve the windows or 

walls of the existing homes. With this in mind, this demonstration focused on reducing cooling and water 

heating loads by replacing existing large equipment with higher-efficiency models. The most costeffective choice for the suite of new appliances was determined using BEopt, a building energy 

optimization software developed at NREL (Christensen, Anderson, Horowitz, Courtney, & Spencer, 

2006). 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
8 

Results from the BEopt simulation for one of the EEE homes are shown in Figures 9 and 10. Beginning 

with a model of the existing house, a set of options to be considered was selected, and utility costs were 

specified. The software then created a model for each possible combination of features, and output the 

cost and energy savings associated with each option, as shown in Figure 9. The total cost takes into 

account the cost to purchase and install a particular option, as well as the effect on the home’s utility bills. 

A detailed comparison by energy end use is shown in Figure 10. 

Figure 9. BEopt optimization curve for one of the EEE homes

Figure 10. Simulated annual energy consumption by end use for pre- and post-retrofit home

In order to address the largest energy consumers in the home, several energy efficiency measures were

installed. The current air conditioning units (approximately SEER 13) were replaced with SEER 21 units. 

In three of the eight homes, a Humiditrol whole-home dehumidification system was also installed to help 

maintain the desired humidity level in the home. The Humiditrol is a product made by Lennox that 

integrates with the air handler, downstream of the evaporator coils. This replaced the existing standalone 

dehumidifier that supplies warmer and dryer air to the intake of the air handler. To control the HVAC 

equipment based on temperature and humidity, a programmable combined thermostat and humidistat was 

installed in all homes, including those that did not have the Humiditrol installed. This gave the residents 

more control over their space-conditioning systems if they chose to take advantage of it. All residents

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
9 

were trained by the installation contractor on how to use their thermostat and the rest of their new 

equipment. Improved dehumidification should lead to improved comfort, not necessarily reduced energy 

consumption, so four temperature and relative humidity (T&RH) sensors were installed throughout each 

house. 

Hot water is the second largest residential energy consumer after HVAC. The existing electric resistance 

water heaters were replaced with HPWHs. The water heaters in each of the EEE homes were located in 

unconditioned spaces—either in the garage or in an outdoor closet. This means the water heaters are

surrounded by warm, humid air all year long, which is the optimal environment for a HPWH. All shower 

fixtures were replaced with low-flow shower heads to reduce hot water consumption as well. A flow 

meter was installed on the water heater to monitor daily hot water consumption before and after the lowflow shower head installation. A T&RH sensor was installed near the HPWH to monitor installed 

performance. 

The homes in each neighborhood are very similar to one another, but different occupants introduce wide 

variability in energy consumption patterns. Air conditioning loads are affected by set point temperature 

and occupant behavior, such as leaving doors or windows open. Dehumidification loads are similarly 

affected by the set point of the dehumidifier and occupant behavior, such as how often they cook or take 

showers. Hot water use is driven by occupant behavior, including how often they do laundry, run the 

dishwasher, and bathe. In addition to improved efficiency in the HVAC system, a programmable 

thermostat was installed in each home. The objective of the demonstration was not to require or expect 

any changes in occupant behavior, but rather to measure “effortless” energy savings achieved by simply 

installing higher-efficiency systems.

3.2 Facility/Site Description

Site selection for the two demonstrations was based on criteria set by NREL. NBG was responsible for 

recruiting residents for the APS demonstration, but participation was strictly voluntary. The EEE homes, 

on the other hand, were chosen by the housing office while they were still vacant. Specific criteria for 

each of the two demonstrations are outlined below. 

3.2.1 Advanced Power Strip Demonstration Sites

Because of the expected large variations in energy savings associated with installing APSs, 30 homes 

participated in this demonstration. The criteria used to recruit participants included: 

• Residents must live in their homes for the duration of the demonstration (through late Fall 2013). 

• Residents have at least a home entertainment center with two devices that can be controlled with 

the APS (such as a DVD player and game console).

• A home office is desired but not required. Similarly, the home office should have at least two

devices that can be controlled with the APS (such as a monitor and printer). 

• Residents must be willing to answer a survey at the beginning and end of the study. 

• Residents must be willing to have their electricity use monitored by NREL during the 

demonstration period. No personally identifiable information is reported in the test results. 

Participant recruitment was conducted by the Facilities Housing division using a combination of the 

following methods: 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
10 

• Distribute “APS Fact Sheet” (see Appendix A) to residents at Town Hall meetings and other 

gatherings to solicit interest. 

• Recruit participants with help from the housing inspectors during the standard intake procedure for 

new residents.

• Work with Barracks Housing Director to recruit residents in the Barracks.

There were 30 homes participating in the APS demonstration. The APS devices deployed in these homes 

are summarized in Table 1. 

Table 1. APS Demonstration Participants

Participating 

Residence

# of APSs in 

Entertainment 

Center

# of APSs in Home 

Office Area

House A 2 1

House B 2 0

House C 1 1

House D 1 0

House E 1 0

House F 1 0

House G 1 1

House H 2 1

House I 1 1

House J 1 1

House K 1 0

House L 1 1

House M 2 0

House N 1 1

House O 1 1

House P 1 0

House Q 1 1

Barracks A 1 1

Barracks B 1 0

Barracks C 0 1

Barracks D 1 0

Barracks E 1 1

Barracks F 1 1

Barracks G 0 1

Barracks H 1 0

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
11 

Participating 

Residence

# of APSs in 

Entertainment 

Center

# of APSs in Home 

Office Area

Barracks I 1 0

Barracks J 1 0

Barracks K 1 1

Barracks L 1 0

Barracks M 1 0

Total 32 16

3.2.2 Enhanced Energy Efficiency Demonstration Sites

The EEE demonstration targeted single-family residential housing that is typical of NBG housing (see 

Figure 11 and Figure 12). Eight homes were selected by the housing staff at NBG for this demonstration

and are listed in Table 2. The homes were chosen because of their location in desirable housing areas, and 

the installed locations and layouts of their HVAC and DHW systems. The detailed criteria used to select 

the EEE homes and their occupants were: 

• Households must have a minimum of two occupants. Families of three or more are preferred.

• Houses must have uninsulated, concrete walls and single-paned windows, to be consistent with the 

majority of homes on NBG. 

• To ensure efficient allocation of resources and maximize demonstration effectiveness, the 

building's HVAC or water heater equipment (preferably both) should be due for an upgrade. 

• Floor plans where water heaters are located in rooms large enough to comply with HPWH 

installation requirements are preferred.

• Occupants must be willing to respond to a questionnaire at demonstration closeout, which includes 

basic questions about their experience with the new appliances. 

• Occupants must be willing to have their electricity use monitored by NREL during the 

demonstration period. No personally identifiable information is reported in the test results. 

While the homes were unoccupied when they were chosen for the demonstration, all prospective residents 

were informed of the details of the project before they moved in. They were given the option of choosing 

a different house if they did not wish to participate. 

Of the eight homes, six are in the same neighborhood (North Tipalao) and are newer homes, all of which 

are part of duplexes. The other two homes are in an older neighborhood (Lockwood Terrace) and are 

detached single-family homes (SFH). All the homes are roughly the same size (1,500 ft2

). The map in 

Figure 13 shows the area where these houses are located. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
12 

Figure 11. Typical residence in Lockwood 

Terrace neighborhood on NBG 

Figure 12. One side of a duplex in the North 

Tipalao neighborhood on NBG

Table 2. EEE Demonstration Participants

Neighborhood Participating Home Notes

Lockwood Terrace Lockwood 1

Lockwood 2 Dehumidifier replaced.

North Tipalao Tipalao 1

Tipalao 2

Tipalao 3 Tipalao 3 and 4 are two sides of duplex unit. 

Dehumidifier was replaced in Tipalao 3. Tipalao 4

Tipalao 5 Dehumidifier replaced.

Tipalao 6

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
13 

Figure 13. Map of EEE demonstration sites

3.3 Monitoring Equipment and Installation

Monitoring equipment was installed in all demonstration locations to measure baseline data before any 

improvements were installed. The same monitoring equipment was also used during the demonstration 

phase to measure the energy consumption and comfort after the new technologies were installed. 

3.3.1 Advanced Power Strip Demonstration Monitoring Equipment

The data for the APS homes were collected by internet-connected Watt’sUp.net meters. The plug load 

meter plugged into the wall outlet, and the power strip for the home entertainment area or home office 

plugged into the meter, allowing the meter to measure the total energy consumed by all devices that were 

plugged into the power strip (and nothing else). This is important because the change in energy 

consumption due to the APS may be small, and it would be difficult to extract the effect of the APS if the 

energy monitoring was done at the circuit breaker level. The plug pass-through meter does not require an 

electrician for installation. 

The Watt’sUp.net meter has an Ethernet port that allows it to upload data to their cloud. A wireless 

hotspot and wireless-to-Ethernet bridge were installed in each home to enable data collection. In homes 

with both a home entertainment center and a home office (or two separate home entertainment centers 

suitable for the demonstration), a single wireless hotspot was installed, but two sets of the Watt’sUp.net 

meter and wireless bridge were needed. A sample of this setup, including the enclosure holding the 

hotspot and bridge, is shown in Figure 14. 

Lockwood Terrace: 

(detached SFH)

• Lockwood 1

• Lockwood 2

North Tipalao: 

(duplexes) 

• Tipalao 1 

• Tipalao 2 

• Tipalao 3 

• Tipalao 4 

• Tipalao 5 

• Tipalao 6 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
14 

Figure 14. A Watt'sUp.net meter setup

The Watt’sUp.net meters collected data every minute and automatically logged the data in their online 

cloud database. Additional details for the Watt’sUp.net meter is listed below in Table 3. 

Table 3. Data Collection Details for APS Demonstration

Meter Description Units Sample

Freq. Accuracy Data Recordingand Backup Data Collector

Watt’sUp.net

Power and 

energy 

consumption of 

electronics

W, Wh 1 min

+/-3% for 

loads >10W 

+/-5% for 

loads <10W

Data recorded in 

cloud automatically, 

downloaded, and 

saved locally

NREL, 

via cloud

After a resident volunteered to participate in the APS demonstration, an NREL researcher or local 

subcontractor scheduled a time to go to their house to install monitoring equipment. The predemonstration questionnaire was filled out the same time the monitoring equipment was installed. A 

laptop was used to check that the Watt’sUp.net meters were uploading data to the cloud before the 

installation was completed. 

There were no calibration requirements for the monitoring equipment. The stated accuracy is +/-3% for 

loads greater than 10 watts (W), and +/-5% for loads below 10 W, which is sufficient for our analysis 

needs. The equipment accuracy is under warranty for 12 months from the date of purchase, long enough 

to cover the duration of the demonstration. 

The remotely accessible data were reviewed at least every two weeks to ensure data were uploaded 

correctly and the results were reasonable. Any issues with connectivity or abnormal data points were

investigated by NREL or local technical resources. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
15 

3.3.2 Enhanced Energy Efficiency Demonstration Monitoring Equipment

The monitoring package for each EEE house consisted of:

• An eMonitor energy monitor system with current transformers (CTs) in the breaker panel to 

monitor the energy consumption of the air conditioner (condenser unit), the air handler, the water 

heater, the dehumidifier, the range, and the dryer, as shown in Figure 15. (The range and dryer 

were not replaced but represent large heat sources that affect cooling loads in the house.) The data 

collected by the eMonitor were uploaded to their cloud via a wireless hotspot. 

• A Minol 130 turbine flow meter was installed on the inlet to the water heater. Pulse output data 

were collected by a HOBO state data logger that was connected to the flow meter. The flow meter 

and state logger are shown in Figure 16. The HOBO logger stores data locally so hot water usage 

data can only be collected from the meter directly. Data collection was done at the conclusion of 

the demonstration period. 

• Five HOBO T&RH sensors were installed around the house, including one installed near the 

HPWH to help determine expected performance. One T&RH sensor was installed next to the 

home’s thermostat, as seen in Figure 17. The other three were installed around the house to 

capture any room-to-room variations in temperature or humidity. These loggers have local storage 

similar to the state logger used with the flow meter. These data were collected at the conclusion of 

the demonstration period. 

The eMonitor system included a wireless gateway that was installed near the breaker panel. A wireless 

hotspot allowed the gateway to upload data from the eMonitor to their cloud. If the eMonitor logger lost 

connection to the internet, it would store up to two weeks’ worth of data. Once the connection was 

reestablished, the locally stored data were uploaded to the cloud. The eMonitor data on the cloud could be 

accessed by NREL at any time and were downloaded regularly to ensure adequate backup. The 

temperature and relative humidity sensors and the state logger for the flow meter could log data for up to 

seven months, but were not accessible remotely. To ensure enough storage space for several months of 

data, the data collection rate was set to record a data point every 15 minutes. All datasets were timestamped in a consistent fashion. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
16 

Figure 15. An eMonitor meter installed in an EEE home with two breaker panels

Figure 16. A flow meter and HOBO state logger at the water heater

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
17 

Figure 17. A T&RH sensor next to the thermostat in an EEE home

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
18 

Table 4. Data Collection Details for EEE Demonstration

Meter Description Units Sample 

Freq. Accuracy Data Recording

and Backup

Data 

Collector

eMonitor

Whole-house 

power and

energy 

consumption

W, Wh 1 min

+/-2% within 

10%-130% range 

of CT rating

Data recorded in 

cloud, downloaded 

at NREL. Logger 

stores data for up 

to 2 weeks.

NREL, via 

cloud

eMonitor

A/C power and

energy 

consumption

W, Wh 1 min

+/-2% within 

10%-130% range 

of CT rating

Data recorded in 

cloud, downloaded 

at NREL. Logger 

stores data for up 

to 2 weeks.

NREL, via 

cloud

eMonitor

Water heating 

power and

energy 

consumption

W, Wh 1 min

+/-2% within 

10%-130% range 

of CT rating

Data recorded in 

cloud, downloaded 

at NREL. Logger 

stores data for up 

to 2 weeks.

NREL, via 

cloud

eMonitor

Range/oven 

power and

energy 

consumption

W, Wh 1 min

+/-2% within 

10%-130% range 

of CT rating

Data recorded in 

cloud, downloaded 

at NREL. Logger 

stores data for up 

to 2 weeks.

NREL, via 

cloud

eMonitor

Clothes dryer 

power and

energy 

consumption

W, Wh 1 min

+/-2% within 

10%-130% range 

of CT rating

Data recorded in 

cloud, downloaded 

at NREL. Logger 

stores data for up 

to 2 weeks.

NREL, via 

cloud

HOBO U12 

T&RH 

sensors

Temperature 

and relative 

humidity

°C, DL 15 min

Temp: ± 0.35°C 

from 0° to 50°C

RH: ± 2.5% from 

10% to 90%

Data saved locally, 

stored for up to 7 

months

NREL or sub, 

manually 

collected on 

site

Minol 130 

turbine flow 

meter, HOBO 

state data 

logger

Hot water 

usage

gallons, 

gpm

15 min AWWA spec

97%-103%

Data saved locally, 

stored for up to 7 

months

NREL or sub, 

manually 

collected on 

site

The eMonitor and CTs were located inside the breaker panel and installed by an electrician. The internet 

gateway that transmits data to the cloud was placed inside a plastic junction box, along with the wireless 

hotspot. This box was mounted on a wall near the breaker panel. All of the HOBO T&RH loggers were 

mounted on walls around the house. They did not need to be housed in enclosures. The flow meter was 

installed by a plumber in the cold water inlet for the water heater. The HOBO state logger was installed

nearby, with a wire connecting the flow meter and the HOBO logger. 

There were no calibration requirements for the monitoring equipment. The manufacturers' stated 

accuracies were sufficient for our analysis needs and are summarized in Table 4. The data were reviewed

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
19 

at least every two weeks to ensure the eMonitor gateway was uploading correctly and the measurements

were reasonable. Any issues with connectivity or abnormal data points were investigated immediately by 

NREL or local technical resources. While the seasonal weather variations in Guam are not significant (it 

is tropical year-round), the energy use data collected during the baseline and demonstration periods were 

used to create year-long simulations for both cases, so as not to bias the results by comparing the energy 

use between two different seasonal periods. The baseline data collection period coincided with the 

warmest part of the year and the demonstration period occurred when the weather was a little cooler. 

Significant occupancy changes due to school holidays (e.g., summer vacation) were evaluated for the best 

approach to account for them in the pre/post comparisons. 

3.4 Baseline Characterization

3.4.1 Advanced Power Strip Demonstration Baseline Testing

Once the monitoring equipment was installed, the baseline characterization began. The residents were

asked to use their electronics as they would normally. The start date and duration of the baseline phase 

was dependent on when the residents were recruited and how much time was available before the end of 

the project. The energy consumption in the home entertainment center and/or home office was measured 

during this time to establish reference conditions. 

Because the participants for the APS demonstration were recruited over several months, the baseline 

monitoring period did not start or end for all homes at the same time. Monitoring equipment for the APS 

homes was installed on a rolling basis so the baseline period varied between homes. NREL did not expect 

noticeable seasonal variability in home entertainment and home energy use (with the possible exception 

of occupancy changes related to school holidays), so a couple of months of baseline data were deemed 

sufficient.

3.4.2 Enhanced Energy Efficiency Demonstration Baseline Testing

For half of the EEE homes, the baseline period began as soon as the monitoring equipment was installed 

in January 2013, as they were occupied by that time. The other homes were unoccupied at the time the 

monitoring equipment was installed, and their baseline testing began once people moved in. The last 

home to be occupied (residents moved in July 2013) had a little over a month of baseline data collected 

before the new equipment was installed. The other homes generated several months of baseline data. 

Because Guam is a cooling climate all year long and there is little seasonal variation, a month of baseline 

data was deemed sufficient as long as there were no extreme weather events during the month. The 

measurements listed in Table 4 were all recorded during the baseline period to establish a reference for 

the energy consumption, indoor comfort conditions, and hot water consumption before the retrofits. 

Local weather datasets from the National Oceanic and Atmospheric Administration (NOAA) website

from the monitoring period were used to drive our energy simulation tool. The simulations were used to 

extrapolate separately the baseline and the demonstration data over a full year for broader comparison. 

This helped us account for changes in weather that could affect space-conditioning energy consumption.

Even though Guam’s weather is fairly consistent over the course of a year, short-term events like tropical 

storms have noticeable impacts on residential energy use. Also, the baseline testing happened to coincide 

with the warmest time of the year and demonstration period was in the slightly cooler fall season, which 

could exaggerate the energy savings if annual simulations are not used for normalization. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
20 

3.5 Demonstration Period

3.5.1 Advanced Power Strip Demonstration

After a minimum of four weeks of monitoring the baseline energy consumption, the residents were mailed 

their APSs with detailed instructions (See Appendix B) on how to set them up. They were also provided 

with contact information for local technical support if they needed additional help. In several cases, a 

local technical support person went to the homes to install the APSs for the residents. Once NREL had 

confirmation the APSs were installed, either by observing a change in the energy consumption data or by 

speaking with the residents, the demonstration period began. The monitoring equipment used for baseline 

data collection remained installed and was used to collect energy use data during the operational testing 

period.

The beginning of the demonstration period varied between volunteers because they signed up at different 

times and they installed their APSs at different times. The first group of homes was fully instrumented in 

late January 2013, and APSs were sent in April. The demonstration period lasted for two to three months, 

so the demonstration for the first group finished in June. The second group of participants had their 

monitoring equipment installed in March and the APSs sent in June. The last group of participants had 

their monitoring equipment installed in July and the APSs sent in September. 

At the conclusion of the demonstration period, the residents were given a final questionnaire designed to 

help NREL assess qualitative aspects of the technology's effectiveness. The monitoring equipment was 

removed, but the APS devices were theirs to keep. 

3.5.2 Enhanced Energy Efficiency Demonstration

The installation of EEE equipment was scheduled for late summer 2013, to ensure that all the homes were 

occupied and we had sufficient baseline data before the demonstration began. Chugach World Services 

was selected through a competitive bidding process to procure and install all the equipment for the eight 

EEE homes. The installations began on July 30, 2013, and were finished a month later, on August 30, 

2013. 

In each home, the water heater was replaced with a 60-gallon A.O. Smith HPWH, and the shower heads 

were replaced with low-flow ones. The condensing unit and air handler for the air conditioner were 

replaced with higher-efficiency Lennox units. The homes in North Tipalao had 3-ton A/C units installed, 

while the slightly larger homes in Lockwood Terrace had 4-ton units installed. In three homes, Lockwood 

2, Tipalao 3, and Tipalao 5, the standalone dehumidifier was replaced with an in-line dehumidifier that is 

installed downstream of the fan coil in the air handler. All the homes had their thermostat replaced with a 

programmable thermostat, which also serves as a humidistat for the homes with new in-line 

dehumidifiers. 

Once the installation of new equipment was completed at each house, the demonstration period began. 

The residents were given training on their new appliances and the thermostat, and were instructed to 

maintain comfort in the home. They were free to change the set points for the water heater and air 

conditioner. The demonstration period lasted two to three months, depending on when their installation 

took place. All monitoring equipment was removed at the beginning of November. All of the energyefficient equipment (the appliances that were upgraded) remained installed and will be maintained by the 

facility staff at NBG.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
21 

3.6 Summary of Performance Objectives

Data were collected before and after the energy-efficiency measures were implemented to evaluate the 

technical objectives of the project. The performance objectives are summarized in Table 5.

Table 5. Performance Objectives

Performance 

Objective Metric Data Requirements Success Criteria

Quantitative Performance Objectives

1 Whole-house energy 

savings Energy (kWh) Whole-house electrical 

energy consumption

10% reduction 

compared to baseline

2 DHW energy 

savings Energy (kWh) DHW electrical energy 

consumption

20% reduction 

compared to baseline

3 HVAC energy 

savings Energy (kWh) A/C electrical energy 

consumption

20% reduction 

compared to baseline

4 Indoor comfort Temperature (C)/ Relative Humidity 

(DL)

Temperature and relative 

humidity measured at 3-4 

locations in each home

Conditions comparable 

or better than before 

while occupants are 

home

5 DHW use reduction Volume 

consumed (gal)

Volumetric flow 

measurement at outlet of 

water heater

20% reduction 

compared to baseline

6

Home entertainment 

center and home 

office plug load 

energy savings

Energy (kWh)

Energy monitor at the 

electrical receptacle 

where APS is located

10%-50% reduction 

compared to baseline, 

depending on type and

vintage of consumer 

electronics used

Qualitative Performance Objectives

1 User satisfaction with 

HPWH

Post-demonstration survey

(see Appendix C and D)

Resident satisfaction 

with implemented 

measures, as indicated 

by survey responses

2 User satisfaction with 

thermostat

3 User satisfaction with 

APS

3.7 Pre- and Post-Demonstration Surveys

The volunteers for the APS demonstration were asked to fill out pre- and post-demonstration 

questionnaires. The pre-demonstration questions asked residents to describe the equipment used in their

home entertainment and office spaces and frequency of use. The post-demonstration questions asked the 

residents whether their new APSs interfered in any way with normal operation of their electronics. The 

pre- and post-demonstration questionnaires are attached in Appendix C. 

The residents of the EEE homes were also asked to fill out post-demonstration questionnaires about their

new equipment. They were asked whether they liked their energy efficient appliances and whether they 

noticed any changes in performance (see survey in Appendix D). Survey results are presented in Section 4. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
22 

4 Technical Performance Analysis and Assessment

4.1 Overview

4.1.1 Overview of Technical Performance for Advanced Power Strip Demonstration

The lengths of the baseline and demonstration periods for each APS house differed depending on when 

the residents signed up to participate. The baseline and demonstration data were analyzed in similar

fashion—the measured energy use was totaled for each day, and the mean daily energy use was computed 

separately for the pre-APS (=“baseline”) and post-APS (=“demonstration”) phases. Data were collected at 

one-minute intervals and uploaded to the Watt’sUp cloud, where it could be downloaded at NREL. The 

internet connection for the Watt’sUp.net meters was provided by cellular hotspots subscribing to a data 

service from Docomo Pacific. The data connection was not always reliable and frequent power outages 

resulted in some lost data. Incomplete days of data were excluded from our analysis. 

4.1.2 Overview of Technical Performance for Enhanced Energy Efficiency

Demonstration

The energy consumption data were logged every minute and uploaded to the eMonitor cloud for remote 

collection at NREL. The eMonitor data logger's gateway used an internet connection provided by a 

cellular hotspot with Docomo Pacific data service. If the internet connection was lost, the eMonitor’s onboard storage could log data for up to two weeks or until the internet connection was restored. The T&RH

sensors and hot water flow meter in each house were standalone loggers with no remote data upload 

capability, so the T&RH and hot water use data for the entire duration of the project were collected at the 

end of the demonstration. The energy measurements allowed NREL to compare the mean daily energy 

consumption before the retrofit and after the new equipment was installed. The T&RH information was 

used to evaluate indoor comfort, and to see whether the residents operated their homes any differently

after the retrofits were installed (e.g., changes in cooling set point). The flow meter was used to measure 

the effect of the low-flow shower heads and determine how much of the reduction in hot water energy use 

can be attributed to the water heater upgrade and how much was caused by a reduction in hot water end 

use.

4.2 Results 

4.2.1 Advanced Power Strip Demonstration Results 

Data collected from the Watt’sUp.net meters was aggregated into daily energy consumption. Many days 

of data were not complete as a result of the persistent connectivity problems. Any day with less than 14 

hours of data (or 60% of the day) was excluded from the analysis. The number of days that had to be 

excluded varied significantly from house to house. Some homes had reliable data throughout, while other 

homes generated only a few days of usable data despite having monitoring equipment installed for 

months. A handful of residences (mostly in the barracks) had monitoring equipment installed, but the 

signal reception for the hotspot was so poor that connectivity problems resulted in no useful data for 

pre/post comparison. Those homes were excluded from the savings analysis. A summary of the total 

number of installations and the reasons why some data were excluded is given in Table 6. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
23 

Table 6. Summary of APS Installations

Total 

Installations

Installations 

that Resulted in 

Useful Data

Reasons Why Some Homes Were 

Excluded

Entertainment 

Center

32 23 • TV was inadvertently left off the energy 

monitor during the pre-APS period so 

unable to do pre/post comparison

• Fewer than 2 total days of post-APS 

data were available

• Data showed no use of electronics after 

APS was installed, so unable to 

compare pre/post

Office 16 12 • Energy use is too small for both preand post-period, indicating no use of 

electronics

• Apparently APS installation was 

followed by a period of zero electronics 

use (resident out of town?) so unable to 

do fair pre/post comparison

• Only 1 day of post-APS data available

The mean daily energy consumption for pre- and post-APS installation for each entertainment center 

installation is given in Table 7. The results from the home office installations are given in Table 8. The 

uncertainties reported for the daily mean energy use are standard deviation of the mean, which dominate 

over sensor accuracy. The predicted annual savings is an extrapolation assuming the mean daily energy 

use in the pre- and post-APS periods provide reasonable estimates for a full year when multiplied by 365. 

Significant variability in the magnitude of expected savings exists across our sample, and this underscores 

the difficulty of this type of demonstration where the signal-to-noise ratio is small for any given house. 

Plug load energy use characteristics are unique to each family, and a large sample size is required to 

achieve statistically meaningful results.

In some cases, the savings number is negative, and this could be explained by a number of things. There 

could have been unusually low use during the baseline period (or equivalently, heavy use after the APS 

was installed). In cases where sample size (number of days of monitoring data) was small, a few outliers 

in the datasets could dramatically impact the mean energy use, and it may be the savings is essentially 

statistically zero. While it is reasonable to expect some homes will not save energy with APS, it is 

difficult to explain increased energy use without a corresponding increase in equipment use unrelated to 

APS installation. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
24 

Table 7. Mean Daily Energy Consumptions for Home Entertainment Center Installations

Residence

Location

Within 

Home

Pre-APS Mean 

Daily Energy Use

(Wh)

Post-APS Mean 

Daily Energy Use

(Wh)

Annual Savings

Predicted

(kWh/yr)

House A Main 3010.3 ±205.1 2673.4 ±109.1 123.0 ±84.8

Bedroom 352.2 ±26.1 509.0 ±50.1 -57.2 ±20.6

House B Main 1315.8 ±75.3 1300.3 ±118.6 5.7 ±51.3

Bedroom 1529.7 ±168.7 442.3 ±25.2 396.9 ±62.3

House C Main 368.7 ±17.9 277.8 ±31.1 33.2 ±13.1

House D Main 3612.8 ±179.4 3482.5 ±171.1 47.6 ±90.5

House E Main 842.2 ±61.3 618.0 ±61.7 81.8 ±31.7

House F Main 2248.3 ±60.3 2014.4 ±337.3 85.4 ±125.1

House G Main 814.8 ±24.6 403.1 ±24.3 150.3 ±12.6

House H Main 2245.2 ±110.5 2756.2 ±507.1 -186.5 ±189.4

Bedroom 1998.6 ±110.3 2819.6 ±1162.6 -299.7 ±426.3

House I Main 845.1 ±32.1 889.1 ±60.5 -16.1 ±25.0

House J Main 1381.0 ±54.4 1088.4 ±107.6 106.8 ±44.0

House K Main 1934.8 ±58.7 482.4 ±50.5 530.1 ±28.3

House L Main 3217.2 ±110.2 2840.3 ±109.6 137.6 ±56.7

House M Main 2513.4 ±67.9 2024.8 ±204.3 178.3 ±78.6

House N Main 1193.4 ±32.2 1040.0 ±74.4 56.0 ±29.6

House O Main 1762.7 ±103.0 1924.8 ±389.9 -59.2 ±147.2

House Q Main 1956.2 ±63.2 1788.5 ±195.6 61.2 ±75.0

Barracks E Main 727.0 ±185.6 2443.2 ±275.9 -626.4 ±121.4

Barracks I Main 197.3 ±37.7 363.5 ±144.6 -60.7 ±54.5

Barracks L Main 1330.7 ±75.4 862.9 ±78.4 170.7 ±39.7

Barracks K Main 578.0 ±60.0 1075.5 ±681.5 -181.6 ±249.7

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
25 

Table 8. Mean Daily Energy Consumption for Home Office Installations

Residence

Pre-APS Mean 

Daily Energy Use

(Wh)

Pre-APS Mean 

Daily Energy Use

(Wh)

Annual Savings

Predicted

(kWh/yr)

House A 2901.4 ±121.8 2427.5 ±132.2 173.0 ±65.6

House C 348.0 ±23.8 282.0 ±26.0 24.1 ±12.9

House G 1576.8 ±23.5 1503.1 ±26.3 26.9 ±12.9

House H 2057.4 ±47.3 1678.8 ±220.0 138.2 ±82.1

House I 1624.3 ±48.2 793.8 ±108.3 303.1 ±43.3

House J 459.3 ±17.2 799.3 ±577.8 -124.1 ±211.0

House L 908.4 ±13.0 887.6 ±11.0 7.6 ±6.2

House N 542.4 ±23.0 597.2 ±34.6 53.5 ±15.1

House O 727.6 ±51.0 763.6 ±88.7 -13.1 ±37.3

House Q 733.8 ±87.2 338.3 ±213.6 144.4 ±84.2

Barracks E 159.1 ±12.5 279.4 ±61.4 -43.9 ±22.9

Barracks K 112.9 ±12.5 48.8 ±7.2 23.4 ±5.2

4.2.2 Enhanced Energy Efficiency Demonstration Results 

Energy use recorded by the eMonitors was totaled for each day, for each circuit measured, and for each 

house. Because of connectivity problems and power outages, there were occasional periods of missing 

data. For brief outages, NREL interpolated the accumulated energy by taking the mean of the adjacent 

timestamps. Where data were missing for longer than one hour, NREL flagged the entire day as 

“incomplete” and disregarded that day's data for pre/post comparison. The mean daily energy savings is 

the difference between the pre-retrofit and post-retrofit daily means. These results are summarized in 

Table 9, Table 10, and Table 11. 

Table 9. Summary of Mean Daily Energy Use for DHW Systems in EEE Homes

Pre-Retrofit Mean 

Daily Energy Use

Post-Retrofit Mean 

Daily Energy Use

Daily Energy 

Savings Percent Savings

(kWh/day) (kWh/day) (kWh/day) (%)

Lockwood 1 4.6 ±0.3 0.9 ±0.1 3.7 ±0.3 79.8

Lockwood 2 6.2 ±0.4 1.5 ±0.1 4.7 ±0.4 75.7

Tipalao 1 5.7 ±0.3 2.1 ±0.2 3.6 ±0.4 63.2

Tipalao 2 6.5 ±0.2 1.7 ±0.1 4.8 ±0.3 73.5

Tipalao 3 3.0 ±0.2 1.1 ±0.1 1.9 ±0.2 63.6

Tipalao 4 5.2 ±0.3 1.6 ±0.1 3.6 ±0.3 68.9

Tipalao 5 N/Aa 

Tipalao 6 4.6 ±0.3 1.8 ±0.1 2.8 ±0.4 61.5

a No water heater energy was measured before the retrofit.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
26 

Table 10. Summary of Mean Daily Energy Use for HVAC Systems in EEE Homes

Pre-Retrofit Mean 

Daily Energy Use

Post-Retrofit Mean 

Daily Energy Use

Daily Energy 

Savings Percent Savings

(kWh/day) (kWh/day) (kWh/day) (%)

Lockwood 1 46.2 ±2.5 34.6 ±1.5 11.6 ±3.0 25.0

Lockwood 2a 69.6 ±3.2 45.0 ±2.1 24.6 ±3.8 35.3

Tipalao 1 31.1 ±1.4 23.0 ±1.8 8.1 ±2.3 26.0

Tipalao 2 46.1 ±1.3 22.2 ±0.9 23.9 ±1.6 51.9

Tipalao 3a 32.8 ±1.3 19.4 ±0.8 13.4 ±1.5 40.8

Tipalao 4 48.8 ±2.0 20.8 ±0.8 28.0 ±2.1 57.4

Tipalao 5a 52.7 ±3.0 36.4 ±2.3 16.2 ±3.8 30.8

Tipalao 6 45.2 ±2.4 32.3 ±1.5 12.9 ±2.8 28.6

a Homes with in-line dehumidifier installed.

Table 11. Summary of Mean Daily Whole House Energy Use for EEE Homes

Pre-Retrofit Mean 

Daily Energy Use

Post-Retrofit Mean 

Daily Energy Use

Daily Energy 

Savings Percent Savings

(kWh/day) (kWh/day) (kWh/day) (%)

Lockwood 1 71.0 ±3.8 53.9 ±2.4 17.1 ±4.5 24.1

Lockwood 2a 96.1 ±4.4 65.4 ±2.8 30.7 ±5.2 32.0

Tipalao 1 56.7 ±2.6 50.7 ±3.8 5.9 ±4.6 10.5

Tipalao 2 86.6 ±2.5 49.0 ±2.0 37.6 ±3.2 43.4

Tipalao 3a 55.5 ±2.2 38.4 ±1.5 17.1 ±2.7 30.8

Tipalao 4 69.4 ±2.7 38.7 ±1.5 30.7 ±3.1 44.3

Tipalao 5a 62.5 ±3.5 46.5 ±2.9 15.9 ±4.6 25.5

Tipalao 6 71.6 ±3.8 57.8 ±2.7 13.9 ±4.6 19.4

a Homes with in-line dehumidifier installed.

Representative daily data for two homes, Lockwood 1 and Tipalao 3, over the demonstration period are 

shown in Figure 18 through Figure 23. These homes were chosen to show typical results from both 

neighborhoods. The energy used by the water heater is shown in Figure 18 and Figure 19. The dates 

marked by a light blue horizontal line indicate dates where data are missing or incomplete. The vertical 

green dotted line corresponds to the date of the retrofit. The red horizontal line shows the mean kilowatthour consumption for the periods before and after the retrofit. While there is clear variability in the dayto-day hot water needs of each house, there is also a marked reduction in the baseline and mean after the 

retrofit. Similar figures follow for HVAC and for whole house for these two homes. The change in hot 

water energy use is most dramatic, but the absolute energy savings for the HVAC system is larger and 

drives the whole-house energy reduction. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
27 

Figure 18. Daily hot water energy consumption for Lockwood 1

Figure 19. Daily hot water energy consumption for Tipalao 3

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
28 

Figure 20. Daily HVAC energy consumption for Lockwood 1

Figure 21. Daily HVAC energy consumption for Tipalao 3

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
29 

Figure 22. Daily household energy use for Lockwood 1

Figure 23. Daily household energy use for Tipalao 3

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
30 

The temperature and relative humidity for each house were monitored during the pre- and post-retrofit 

periods to evaluate whether there were marked changes in indoor conditions that could indicate a change 

in occupant comfort level. As summarized in Table 12, there was little change in indoor conditions after 

the new equipment was installed. While the relative humidity tended to increase in the homes after the 

retrofit, all conditions meet American Society of Heating, Refrigerating and Air Conditioning Engineers 

(ASHRAE) standards for comfort. The increase in humidity inside the homes also coincided with an 

increase in humidity outside (see Figure 26). The uncertainties given are the statistical variations in the 

day-to-day mean; errors due to sensor accuracy are negligible compared to the standard deviations. 

Table 12. Indoor Conditions Before and After the Retrofit for all EEE Homes

Pre-Retrofit 

Mean Temp

(°F)

Post-Retrofit 

Mean Temp

(°F )

Pre-Retrofit 

Mean RH

 (%)

Post-Retrofit 

Mean RH

(%)

Lockwood 1 71.6 ±0.2 71.6 ±0.2 50.4 ±0.3 54.8 ±0.4

Lockwood 2a 72.7 ±0.1 71.8 ±0.2 50.7 ±0.2 58.6 ±1.2

Tipalao 1 77.3 ±0.1 79.4 ±0.4 43.6 ±0.2 36.2 ±0.8

Tipalao 2 74.4 ±0.1 77.4 ±0.6 44.9 ±0.2 41.9 ±0.6

Tipalao 3a 74.9 ±0.1 75.1 ±0.1 41.5 ±0.3 40.5 ±0.3

Tipalao 4 75.2 ±0.1 73.7 ±0.1 44.9 ±0.4 57.7 ±0.4

Tipalao 5a 72.7 ±0.4 69.4 ±0.3 51.8 ±0.4 55.6 ±0.2

Tipalao 6 76.1 ±0.1 75.1 ±0.2 42.4 ±0.2 53.8 ±0.8

a Homes with in-line dehumidifier installed.

Low-flow shower heads were installed at the same time as the HPWH, so some DHW energy savings 

may be attributable to a reduction in shower hot water use. The mean daily hot water consumption before 

and after the retrofit was computed and the results are given in Table 13. NREL does not know the flow 

rate of the original shower heads, and they may have been different for different homes. The uncertainties 

are standard deviation of the mean, which dominate over sensor accuracy. 

Table 13. Summary of Hot Water Usage per House

Pre-Retrofit

Hot Water Use

(gal/day)

Post-Retrofit Hot 

Water Use

(gal/day)

Hot Water 

Savings

(%)

Lockwood 1 31.3 ±1.8 32.5 ±2.0 -4.0 ±2.7

Lockwood 2a 71.8 ±3.9 49.8 ±5.2 30.6 ±6.5

Tipalao 1 50.7 ±2.6 36.7 ±18.3 27.7 ±18.5

Tipalao 2 N/Aa 

Tipalao 3a 52.9 ±2.4 35.1 ±6.8 33.6 ±7.2

Tipalao 4 66.2 ±3.6 73.0 ±4.2 -10.3 ±5.5

Tipalao 5a 10.8 ±2.0 10.2 ±2.3 5.8 ±3.1

Tipalao 6 36.7 ±2.6 50.8 ±2.3 -38.5 ±3.5

a The HOBO flow meter was defective. No flow data was collected.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
31 

4.3 Energy Model Simulations

4.3.1 Annual Energy Use Simulation for Advanced Power Strip Homes

As the demonstration period was less than a year in duration, an energy model was generated and 

calibrated to generate annual energy savings estimates. Year-long simulations were performed for the 

EEE homes, but not for the APS homes. Because of the variability in how people use their electronics, 

simulations may be able to approximate the effect of APSs in an average house but are not detailed 

enough to predict the savings for a single house and its unique residents. 

4.3.2 Annual Energy Use Simulation for Enhanced Energy Efficiency Homes

The results from the EEE demonstrations were used to calibrate simulation models for each home in 

BEopt. Figure 24 and Figure 25 show houses from both neighborhoods as they are represented in BEopt. 

Annual simulation results were used to determine annual energy savings, which takes into account 

weather differences between the baseline and demonstration periods. Even though the climate in Guam 

does not vary significantly over the course of a year, there are still seasonal variations in weather between 

the baseline and demonstration periods that could impact the results. Figure 26 shows the average dry 

bulb temperature and relative humidity for every day of the past year. The data came from a NOAA 

weather station at the Guam International Airport (NOAA, 2013). The baseline data collection occurred 

during the hottest part of the summer, and the demonstration period was later in the fall, when the average 

temperature was slightly lower. As a result, neglecting to account for changes in weather would make the 

reduction in HVAC energy use appear artificially high. These annual BEopt energy simulations enable 

fair comparison of the baseline and demonstration data and give a conservative estimate for annual energy 

savings achieved though the demonstration. 

Figure 24. BEopt model for a Lockwood Terrace 

home

Figure 25. BEopt model for a North Tipalao 

home (half a duplex shown)

Two distinct models for each home were created to simulate the pre-retrofit home and the post-retrofit 

home. The pre-retrofit model was used during the design stage to determine the most cost-effective 

retrofit measures, as described in Section 3.1.2. That model was created based on the physical attributes of 

the house and details of the existing equipment. The process of matching pre-retrofit data to the preretrofit simulation results began with this base model. Local weather data for the past year was loaded into 

the simulation engine to ensure the model was referencing the same conditions the home experienced. 

With the physical details of the home and actual weather conditions captured by the model, the remaining 

differences are tied to the residents’ preferences. The temperature and humidity set points were adjusted 

so the simulated HVAC energy use matched with the actual HVAC energy use. Daily hot water use and 

water heater set point were modified to match the simulated hot water energy use to the data. The 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
32 

measured indoor conditions and hot water use were used to help calibrate the model. A similar process 

was followed for the post-retrofit home model. The post-retrofit model was physically identical to the preretrofit model, except for the new energy efficiency equipment that was installed during the retrofit. The 

same year of weather was used for the post-retrofit simulations. 

Figure 26. Outdoor temperature and humidity over the past year in Guam

Source: NOAA, 2013

It was not feasible to calibrate the model based on every day of data, and there were some days of data 

missing as a result of power outages and dropped communications. Average daily energy use over several 

weeks was used for comparison instead. The daily energy for the HVAC system, water heater, and the 

whole house was averaged over several months in chunks before and after the retrofit. The mean daily 

HVAC energy use over several two-to-four week-long periods in June and July were compared to the preretrofit simulation results for the same periods. The post-retrofit data in September and October were 

similarly compared to simulated energy use. When possible, the model was calibrated until the simulation 

results matched the data to within 5% for each period for HVAC, DHW, and whole-house daily energy 

use. There were some instances where the model could not be adjusted to match all the months 

considered, and in those cases, it was calibrated until the error over all the months summed to zero. For 

example, a pre-retrofit model where the difference between modeled and measured in June was -12% and 

+12% in July would be considered a good match to the data. 

Figure 27 and Figure 28 show how well the modeled and measured data match for HVAC energy use and 

DHW energy use during the time periods used for calibration. The dotted line on the diagonal represents 

perfect agreement between measured data and simulation. The black squares and black points are the preand post-retrofit energy use, respectively. The y-axis error bars represent the statistical uncertainty in the 

measured mean energy use; they are plus/minus one standard deviation of the mean. The error bars are 

color-coded by house. With few exceptions, the measured value is within one sigma of the corresponding 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
33 

modeled value. The reduction in energy use after the retrofit is apparent in both measured and simulated 

data. For example, in Figure 27, the cluster of squares with red error bars near 70-80 kilowatt-hours 

(kWh) in both x- and y-axes correspond to the mean daily energy use for Lockwood 2 computed over 

three time intervals before the retrofit installations. The cluster of points with red error bars near 45 kWh 

in both x- and y-axes corresponds to the post-retrofit mean daily energy use for the same house.

Figure 27. Measured vs. modeled HVAC mean daily energy use

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
34 

Figure 28. Measured vs. modeled DHW mean daily energy use

Once the pre-retrofit and post-retrofit models were well-matched with the data, simulated annual use was 

calculated for HVAC, DHW, and whole house. The difference between the annual energy use in the preand post-retrofit models is the estimated annual savings. Table 14 summarizes these results. The cost 

savings were calculated using the current electricity price in Guam of 50¢/kWh. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
35 

Table 14. Annual Simulation Results 

HVAC Annual 

Energy Savings

DHW Annual 

Energy Savings

Combined Annual 

Energy Savings

Expected Annual 

Cost Savings

(kWh) (%) (kWh) (%) (kWh) ($) 

Lockwood 1 710 5 1430 80 2140 1070

Lockwood 2a 4600 21 1740 76 6340 3170

Tipalao 1 1470 14 1450 65 2920 1460

Tipalao 2 6200 41 1780 75 7980 3990

Tipalao 3a 3200 30 800 67 4000 2000

Tipalao 4 7860 49 1400 71 9260 4630

Tipalao 5a 4080 23 N/Ab N/A 4080 2040

Tipalao 6 3240 20 1080 63 4320 2160

Mean 3920 1380 5130 2570

Standard Dev. 

of Mean

830 130 880 820 440

a Homes with in-line dehumidifier installed.

b No water heater energy was measured before the retrofit.

4.4 Analysis of Results

4.4.1 Advanced Power Strip Demonstration Results Analysis

To estimate the annual energy savings from all data, NREL employed a maximum likelihood estimator 

with two free parameters: net savings (kilowatt-hours/year), and intrinsic scatter (kilowatt-hours/year). 

The second parameter accounts for the variation in savings from home to home due to factors other than 

measurement error (i.e., variation in user behavior, etc.). NREL then marginalized over this “nuisance” 

parameter to obtain a maximum likelihood net savings and uncertainty. With this method, the reported 

uncertainty in the net savings accounts for both measurement error and home-to-home variation due to 

user behavior and other factors. Table 15 gives results (with 68% confidence interval) with intrinsic 

scatter taken into account.

Table 15. Annual Energy Savings from APS

Energy Annual Energy 

Savings for any House

Corresponding Annual 

Cost Savings

(kWh) ($) 

Entertainment Center 58 ± 44 29 ± 22

Office 40 ± 24 20 ± 16

To illustrate the variability in the APS results, data from two homes are highlighted below. The main way 

that APSs reduce energy use is by reducing the standby power consumption. Any electronics that are 

plugged into controlled outlets will be completely turned off by the APS when they are not in use. This 

impact can be seen by looking at the power consumption over time. Figure 29 shows the entertainment 

center from House G and is an example of how this looks in an ideal installation. The power consumption 

when the electronics are on is unchanged, but the baseline, which is the steady standby power that is 

always on, drops from 20 W to 0 W after the APS is installed. It is rare to see the standby power drop to 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
36 

zero, as there are usually a few devices that need to remain on all time, like a cable box or modem. In this 

particular house, eliminating the standby power consumption reduced the daily mean energy use by 50% 

or about 150 kWh/year. The daily reduction in energy use is also evident in the distribution of pre- and 

post-APS daily energy use, as shown in Figure 30. 

Figure 29. Home entertainment center power consumption in House G before and after APS

Figure 30. Histogram of entertainment center daily energy use in House G before and after 

APS

5/3/13 5/6/13 5/9/13 0

20

40

60

80

100

120

140

Power (W)

4/14/13 4/17/13 4/20/13 0

20

40

60

80

100

120

140

Power (W)

Pre-APS Post-APS

0 500 1000 1500

0

3

6

9

12

15

19

Average Daily Energy Use (Wh)

Number of Days for Pre-APS test

Distribution of Daily Energy Use Home Entertainment Center

0

21

Number of Days for Post-APS test

Pre-APS

Post-APS

Power consumption for House G

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
37 

In contrast to the ideal case shown for House G above, the results from a bedroom entertainment center 

installation in House A are shown in Figure 31 and Figure 32. The daily mean energy use for this case 

increases significantly after the APS is installed, but the power trace helps to explain this result. A week 

of pre-APS power consumption shows the entertainment system was rarely used and a week of post-APS 

power consumption shows much more frequent activity. This installation is in the children’s bedroom, 

and the APS installation happened to coincide with the beginning of summer vacation. The standby power 

level is basically unchanged, which may indicate there were few items in the entertainment center that 

could be controlled by the APS (in other words, most devices had to be plugged into the “always on” 

outlets). The lack of reduction in the standby power and the increase in use of the entertainment center 

resulted in a 44% increase in daily energy use, but in reality, this APS likely had little impact on the

energy use of the electronics, and the increase was an artifact of changes in occupant behavior.

Figure 31. Home entertainment center power consumption in House A before and after APS

8/8/13 8/10/13 8/12/13 0

50

100

150

Power (W)

3/18/13 3/20/13 3/22/13 0

50

100

150

Power (W)

Pre-APS Post-APS

Power consumption for House A

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
38 

Figure 32. Histogram of entertainment center daily energy use in House A 

before and after APS

Changes in user habits can have a big impact on the apparent energy savings (or lack thereof) after an

APS is installed. In the case of House A, NREL knew enough about the residents and the installation to 

make an educated guess as to why the energy consumption increased, but that was the exception rather 

than the rule. For many of the homes, interactions with residents were much more limited, and it has been 

difficult to explain all of the unexpected features in the distributions. To add to these complexities, people 

introduced new electronics frequently and that was another factor difficult to capture in this 

demonstration. 

When APSs are installed correctly, they should reduce the standby power consumption, leading to a 

decrease in daily energy consumption, even if that decrease is small. Any increase in energy use is likely 

due to changes in usage patterns or changes to the electronics in the entertainment center or home office. 

4.4.2 Enhanced Energy Efficiency Demonstration Results Analysis

The EEE demonstration was an overall success, with all homes saving energy in both cooling and hot 

water use. Despite the fact all the homes were similar in size and family demographics, the energy use and 

energy savings between the homes varied significantly. 

The installation of the HPWH saved at least 60% of DHW energy in all homes, but there was little 

consistency in how the low-flow shower heads affected water use or energy use. The homes that 

experienced reductions in hot water use after the low-flow shower heads were installed did not save more 

energy than those that actually increased their daily hot water use. It is unclear why the low-flow shower 

heads had so little impact on the daily hot water use in the EEE homes, but it is possible that some homes 

already had low-flow shower heads, as the facility staff did not have any information on the existing 

shower heads. NREL also heard from a couple of residents that they had handheld shower heads so they 

never used their low-flow shower heads, which are fixed to the wall. Additionally, in homes with young 

children where baths are more common than showers, the shower heads in the children’s bathroom may 

never have been used. 

0 500 1000 1500

0

3

6

9

12

15

17

Average Daily Energy Use (Wh)

Number of Days for Pre-APS test

Distribution of Daily Energy Use Bedroom Entertainment Center

0

16

Number of Days for Post-APS test

Pre-APS

Post-APS

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
39 

HVAC savings were achieved in all homes and the magnitude of those savings varied between the homes. 

In general, the smallest savings were seen in the homes with the lowest average indoor temperature or 

lowest indoor relative humidity. The homes that saved the most energy allowed their homes to stay 

warmer and more humid (though still well within the comfort region as defined by ASHRAE). Residents 

from the two homes that saved the most energy (Tipalao 2 and Tipalao 4) both said they turned off their 

standalone dehumidifiers after the new air conditioners were installed, as they felt the new A/C was able 

to maintain low humidity better than the old system. Turning off the dehumidifier made the house quieter 

and also saved a large amount of energy without sacrificing comfort. 

Replacing the standalone dehumidifier with in-line dehumidifiers had no obvious impact on the humidity 

levels or energy use in the homes. The humidistat gave residents more control over the humidity levels in 

their homes, but there was no consistent trend between the three homes with the in-line dehumidifiers in 

terms of reduced humidity or relative energy savings. The in-line dehumidifiers are quieter than the 

standalone dehumidifiers so they improve the noise comfort in the homes. NREL received feedback from 

one resident with the in-line dehumidifier that their house stayed too cold (always below the set point 

temperature), possibly indicating an issue with the reheat system downstream of the dehumidifier coils. 

This was not an issue in the other homes with the in-line dehumidifier so it is unclear what caused the 

over-cooling problem.2

 

In general, installing high-efficiency air conditioners and HPWHs can significantly reduce energy use, 

regardless of how the residents like to control their house or how much hot water they use. The in-line 

dehumidifiers were not found to be an improvement and in one case, actually affected the comfort 

adversely, albeit for reasons unknown. The standalone dehumidifiers appear to be a good solution for 

people who want dryer air, but may not be needed for all households. Low-flow shower heads did not 

show a consistent effect on daily hot water usage but should still be installed in new homes to avoid 

needlessly wasting hot water. 

4.5 User Feedback and Survey Results

4.5.1 Advanced Power Strip User Feedback

The APS surveys were handed out when the monitoring equipment was removed, but not many were 

completed. 

Very few people installed their APSs on their own. A local contractor followed up with residents and 

installed the APSs for them in most cases. Generally, there was no explicit reason given why the residents 

did not install their APSs, other than that people are busy and this is a tedious task that would disrupt plug 

load use for a short time. However, once the APSs were installed and the functionality was described to 

the residents, people seemed open to the minor changes the APSs may require in how they normally 

operate their electronics. Even one resident with a large entertainment center in his converted garage had 

volunteered for the demonstration and was amenable to the usability changes that were part of the APS 

installation. 

4.5.2 Enhanced Energy Efficiency User Feedback

For the EEE homes, user feedback was collected almost entirely with the post-demonstration surveys that 

were distributed when the monitoring equipment was removed. The comments were generally positive. 

 

2 The over-cooling problem was corrected temporarily by turning off the dehumidifier. NREL will have the installation 

contractor follow up to evaluate whether there is a defect with the unit. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
40 

People were impressed with the new modern equipment, especially the look of the new thermostat 

(though only two households had set up a regular thermostat schedule). The new air conditioner was very 

favorably received, with everyone noting it was much quieter than the original system and did not run as 

often. A few residents found that the new air conditioner was able to remove more moisture than the old 

system so they stopped using the standalone dehumidifier. Residents noticed that the HPWH made noise, 

unlike the original electric resistance water heater, but nobody indicated whether the noise was 

bothersome. The water heaters in this demonstration were installed either in the garage or an outdoor 

closet, so the noise from the HPWH did not have a big impact on the living space. Some residents had 

turned up their set point to compensate for the slower recovery time for the HPWH, but they were happy 

with the water heater after the adjustment. The low-flow shower head received mixed reviews, but most 

people said they would buy low-flow shower heads in the future, even if they liked the higher-flow rate 

shower head better. The in-line dehumidifier also had mixed reviews, with one resident saying the house 

was always colder than the set point. The other two homes with the in-line dehumidifier did not have this 

issue, so it is unclear what caused the over-cooling. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
41 

4.6 Assessment of Performance Objectives

Table 16. Assessment of Performance Objectives

Performance 

Objective Success Criteria Outcome

Quantitative Performance Objectives

1 Whole-house energy 

saving

10% reduction compared 

to baseline

Success—Mean savings of 20% over baseline 

from the simulations. 

2 DHW energy saving 20% reduction compared 

to baseline

Success—Mean savings of 70% over baseline 

from simulations. 

3 HVAC energy saving 20% reduction compared 

to baseline

Success—Mean savings of 25% over baseline 

from simulations. 

4 

Indoor comfort Conditions comparable or 

better than before while 

occupants are home

Success—Indoor conditions were comparable 

or better. Occupants enjoyed the quieter 

system, as well. 

5 DHW use reduction 20% reduction compared 

to baseline

Inconclusive—Some homes used less hot 

water on average per day and some did not. It 

is possible that some of the existing shower 

heads were already low-flow models. 

6 

Home entertainment 

center and home 

office plug load 

energy savings

10%-50% reduction 

compared to baseline, 

depending on type and

vintage of consumer 

electronics used

Limited Success—Median decrease in daily 

energy use of 10% for AV environment and 

11% for PC environment. Results vary 

significantly from house to house. Energy use 

increased after APS installation in several 

homes.

Qualitative Performance Objectives

1 User satisfaction with 

HPWH

Resident satisfaction with 

implemented measures, 

as indicated by survey 

responses

Success—All residents were happy with their 

HPWH.

2 User satisfaction with 

thermostat

Success—All residents were happy with their 

thermostat (though few were using its 

programmable functions). 

3 User satisfaction with 

APS

Unknown—No APS surveys collected at this 

time.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
42 

5 Economic Performance Analysis and Assessment 

5.1 Economic Performance of Advanced Power Strip Demonstration 

Economic results of the APS demonstration were not positive, indicating deployment of this technology 

in a military housing environment may not yield appreciable savings without further study to evaluate 

effective options to implementation. In demonstration of the APS devices, annual energy savings is 

estimated at 100 kWh/yr. Accounting for initial investment costs and a high, estimated attrition rate in 

APS usage over a four-year economic life, net savings comes in at a negative balance. For a follow-on, 

large-scale deployment initial investment cost per residence is projected to be significantly reduced. Net 

savings is estimated at $20 per household over a four-year economic life; however, the statistical 

confidence in this estimate is low, owing to the high variability in observed energy savings. 

A key factor affecting economic results is the estimated, high attrition rate of APS usage over a four-year 

economic life. This attrition rate is attributed to residents moving to their new posts after completing their 

Guam tour and failing to install their APS devices correctly (or at all) when they set up their entertainment 

centers or home offices in their new residences. The originally deployed APS devices may be lost in the 

move. Owing to the high turnover rate of residents in military housing, this study estimates that 25% of 

the originally installed APS devices are not utilized in the subsequent year. More specifically, usage 

estimates are 100% in the first year, 75% in the second year, 50% in the third year, and only 25% of the 

originally deployed APS devices in the fourth year. If the actual attrition rate in a deployed environment 

can be significantly less than these estimates without appreciable new costs, the economic viability of 

these devices would be greatly improved. 

Table 17 provides a full summary of economic results, in addition to key analysis inputs. Estimates for net 

savings and simple payback were calculated using the latest version of the National Institute of Standards 

and Technology (NIST)-developed Building Life-Cycle Cost (BLCC) program. A detailed accounting of 

the economic analysis performed can be found in Appendix E. 

Table 17. Economic Analysis of APS Demonstration

Demo Actuals Projected Follow-On 

Economic Analysis Results

Net Savings, Four-Year Life -$480 $20 +/- $60 

SIR, Five-Year Life N/A 1.1 

Adjusted Internal Rate of Return N/A 5.2% 

Key Analysis Inputs

Annual Energy Savings 100 +/- 50 kWh 100 +/- 50 kWh 

Electricity Price $0.50/kWh $0.50/kWh 

Initial Investment Cost $600 $100 

Economic Life 4 years 4 years

5.2 Economic Performance of Enhanced Energy Efficiency Demonstration 

Economic results of the EEE demonstration indicate application of the EEE technologies in Joint Region 

Marianas (JRM) can yield appreciable energy and cost savings. In demonstration of the EEE retrofit 

packages at eight NBG residences, the aggregate, annual energy savings is estimated at 40 megawatthours (MWh)/yr. In comparison to a minimally efficient retrofit of similar quality to the replaced 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
43 

equipment, NREL estimates a net savings of $120,000 over a 10-year operational life, with an adjusted 

internal rate of return of 16% per annum. Results are promising and indicate the U.S. Navy, on an 

economic basis, should consider further investment and deployment of these technologies—at least in 

tropical climates similar to the U.S. Territory of Guam. 

Table 18 provides a full summary of economic results, in addition to key analysis inputs. Estimates for net 

savings, savings-to-investment ratio (SIR), and simple payback were calculated using the latest version of 

the NIST-developed BLCC program. Energy return on investment (eROI) values were provided using the 

latest available version of the Neptune eROI calculator, as provided by Naval Facilities Engineering 

Command (NAVFAC).3

 A detailed accounting of the economic analysis performed can be found in 

Appendix E. 

Table 18. Overall Economic Analysis of EEE Demonstration

Economic Analysis Results Key Analysis Inputs

eROI Value 10.1 Annual Energy Savings 40 +/- 7 MWh

Net Savings, 10 years $120,000 Electricity Pricea $0.50/kWh

SIR 3.3 Investment Cost Deltab $56,808

Simple Payback <3 years Units Installed 8 

Adjusted Internal Rate of Return 16% Economic Life 10 Years

a “Electricity Price” reflects fiscal year 2014 rates at JRM. b

 “Investment Cost Delta” reflects the calculated difference in investment cost between the installation of the enhanced 

energy efficiency equipment versus the hypothetical installation of a minimally energy efficient set of equipment (see 

Appendix E for more details). Intent of the investment delta is to infer the economic value of retrofitting residences with 

enhanced efficiency elements versus retrofitting with minimally efficient equipment of similar pre-retrofit performance 

levels. 

In addition to the aggregate return of the EEE retrofits, performance was also evaluated for the individual 

contributions of the EEE package’s domestic water and HVAC technologies. Economic returns were 

significant for both respective technology offerings. On a per unit basis, the DHW technologies (HPWH 

and low-flow shower head) showed an average, annual energy savings of 1,400 kWh/yr. The highefficiency HVAC units showed an average savings of 4,000 kWh/yr. 

Table 19 provides a full summary of results on a per unit basis. 

 

3 eROI is a U.S. Navy specific metric for evaluating benefits of investment in energy technologies. The benefit figure reflects 

the present value of the project’s anticipated contribution to energy as well as its contribution, in dollar-equivalent terms, to 

other U.S. Navy objectives, such as improving energy reliability for critical infrastructure, reducing greenhouse gas emissions, 

meeting regulatory mandates, and so on. An eROI greater than 1.0 indicates the project’s benefits are anticipated to exceed its 

costs. The higher the eROI value, the more attractive the project.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
44 

Table 19. Economic Analysis of EEE Demonstration on a per Unit Basis

DHW Results per Unit HVAC Results per Unita

Annual Energy Savings 1.4 +/- 0.1 MWh Annual Energy Savings 4.0 +/- 0.8 MWh

Net Savings, 10 years $4,500 Net Savings, 10 years $11,000

SIR 3.9 SIR 2.9

Simple Payback <3 Years Simple Payback <4 Years

Adjusted Internal Rate of Return 18% Adjusted Internal Rate of 

Return 14%

Investment Cost Deltab $1,700 Investment Cost Deltab $6,500

a HVAC economic analysis excludes costs relating to the whole-house dehumidifiers. Evaluation of results indicates these 

dehumidifiers did not present statistically significant savings and were therefore removed from the economic analysis.

b

 “Investment Cost Delta” reflects the calculated difference in investment cost between the installation of the enhanced energy 

efficiency equipment versus the hypothetical installation of a minimally energy efficient set of equipment (see Appendix E for 

more details). Intent of the investment delta is to infer the economic value of retrofitting residences with enhanced efficiency 

elements versus retrofitting with minimally efficient equipment of similar pre-retrofit performance levels. 

As evident in Table 19, application of the DHW technologies presented the best return per dollar invested, 

with an adjusted internal rate of return (AIRR) of 18% and a SIR of 3.9. HVAC technologies also show a 

promising return, excluding use of the whole-house dehumidifier, with an AIRR of 14% and SIR of 2.9. 

The whole-house dehumidifier did not show statistically significant savings. 

Economic results were reviewed to evaluate potential sources of error and/or uncertainty in the estimates 

provided. Four issues were identified and are described below. 

• Utility electricity rate volatility. Significant escalation in JRM utility rates from fiscal year (FY) 

2013 to FY14 indicate analysis results as presented may be susceptible to uncertainty in projecting 

future utility rate pricing. More specifically, utility rates have jumped from $0.2984/kWh in FY13 

to $0.4995/kWh in FY14. Based on these recent rate adjustments, forecasting future year utility 

rates is challenging, especially over a 10-year economic life. In addition, BLCC escalation rates 

were not available for Guam in providing an authoritative, reference benchmark. Accounting for 

the utility rate uncertainty and lack of availability of a BLCC benchmark, the analysis concluded 

forecasting future escalation rates could not be appropriately determined. Therefore, escalation of 

rates over the economic life of the study was not assumed; however, over the next 10 years 

escalation in utility rates is possible, if not likely, and should be noted as a potential source of 

error in the analysis. In this sense, the results are likely indicative of a lower limit to savings 

achievable; if rates go up, cost savings and SIR will increase.

• Statistical variance in energy savings. Significant variability in energy saving results was 

observed between the eight households, especially with respect to HVAC-related savings (see

Table 9 through Table 11. Estimated annual energy savings for the HVAC systems over the eight 

residences range from 700 to 7,900 kWh/yr, whereas DHW savings ranged from 800 to 1,800 

kWh/yr. The wide distribution in savings, especially for HVAC systems, is likely attributable, in 

part, to differences in behavioral dynamics among the residents. Residents were allowed to adjust 

temperature set points to meet their preferences, which will directly impact absolute savings. For 

example, if residents were low-volume hot water users, the water heater would not be used as 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
45 

much and the absolute savings would be less pronounced. This variability presents a statistical

uncertainty to the results, which should be noted when evaluating average, annual energy savings 

and economic yield. The standard deviation of the mean for the aggregate annual energy savings 

of the EEE retrofits is +/-7,000 kWh. For DHW savings per unit, the value is +/- 100 kWh, and for 

HVAC savings per unit, the value is +/- 800 kWh. These values, although appreciable, do not 

significantly alter the conclusions drawn by the economic analysis. 

Figure 33. Annual HVAC and DHW savings per house

• Uncertainties associated with calibrating BEopt models using measured data. There are some 

fundamental challenges with the study’s method to account for the change in season from summer 

to fall over the course of the demonstration period. The annual energy savings estimated using this 

approach was dramatically less than a simple projection of the measured savings because the 

weather was cooler after the retrofits, so a significant fraction of the energy reduction was 

attributed to the decrease in cooling load rather than an increase in equipment efficiency. 

Nevertheless, this method was chosen to ensure against overprediction of savings. It should be 

noted the actions recommended in this report would remain unchanged whether the measured 

savings or calibrated modeled savings was used. 

• Investment cost estimates. Evaluation of the economic return is dependent upon accurate 

estimation of costs of replacing the existing residential HVAC and DHW equipment with EEE 

retrofits in comparison to replacing them with a less expensive and less energy efficient options. 

More specifically, a key economic metric of this demonstration is to determine whether the greater 

performance of the EEE retrofits outweighs its added investment cost relative to a less expensive 

option. The EEE retrofits were installed using a competitively selected contractor. Costs for the 

EEE retrofit installations are therefore competitively priced and fully defined by accounting of 

project actuals. Costs of a less expensive option, however, were not realized on this project. These 

costs were estimated for this analysis and are susceptible to error. To account for potential error, 

the analysis used conservative, minimum pricing of comparative options to ensure economic 

yields are not positively biased. As an example, the least expensive equipment option on the U.S. 

General Services Administration schedule was used for each HVAC and DHW element priced, 

specified at the performance levels of the equipment replaced by the EEE retrofits. Additional 

detail is provided in Appendix E. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
46 

6 Project Management Considerations

For both the EEE and APS demonstrations, programmatic activities were straightforward with limited 

challenges. The EEE demonstration used a local contractor for procurement and installation of 

demonstration equipment. For the APS demonstration, devices were procured by NREL and delivered to 

each respective resident. Each resident then self-performed installation of the APS devices or received 

help with the installation from an on-island contractor. For both demonstrations, the commercial 

availability of the demonstrated technologies made for easy acquisition and deployment. Table 20

provides a summary of programmatic elements of these demonstrations and a high-level timeline of 

events.

Table 20. Summary of Programmatic Elements for APS and EEE Demonstrations

Programmatic Summary—APS Demonstration

Implementation Method NREL Procurement, Resident Self-Performed Installation

Key Contractors None

Period of Performance 16 Months 

Project Timeline May 2012 NBG Housing Approves Demonstration

June 2012 to May 2013a Recruitment of NBG Residents

April 2013 to Sept. 2013b APS Installations

Programmatic Summary—EEE Demonstration

Implementation Method Service Contract for Procurement and Installation

Key Contractors Chugach World Services, Inc.

Period of Performance 16 Months 

Project Timeline May 2012 NBG Housing Approves Demonstration

Nov. 2012 Residences Identified

Jan. 2013 to July 2013 Pre-Install, Baseline Measurements 

May 2013 to Aug. 2013 EEE Installations

a Recruiting residents took significantly longer than expected. Several factors contributed to this; however, the 

primary challenge was gaining resident interest and election to participate in the demonstration.

b The significant time investment in APS installation may be misleading. APS installations were staggered as new 

residents signed on to participate in the demonstration. Actual time needed to perform APS install was negligible (on

the order of a month for procurement, delivery, and install). 

Further deployment of the EEE or APS technologies in a military housing environment should not require 

unique or sophisticated acquisition strategies. Some of the lessons learned from these demonstrations, 

however, may lend value in future deployments and are listed below: 

• APS “elect-in” vs. “elect-out” participation. For future APS deployments, a key consideration 

will be determining the best approach to selecting residences. The demonstration used an elect-in 

approach, where residents elected to participate. This required significant upfront time and 

expense in educating residents and “selling them” on electing to participate. This approach yielded 

limited participation. In contrast, an elect-out approach, in which all residents participate unless 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
47 

they elect-out, may yield a more efficient approach to large-scale deployment, both in respect to 

deployment time and level of participation. 

• APS proper installation and operation. Based on energy savings results, NREL believes a 

significant fraction of residents who received APS devices did not properly install the devices. 

Additional training or a different approach to installation of the APS devices should be considered 

to improve deployment effectiveness. 

• EEE design considerations. Some of the EEE equipment will require a few, unique design 

requirements going beyond standard commercial offerings. These requirements should be noted 

for future retrofits. For example, high-efficiency outdoor condensers require a larger physical 

footprint in comparison to nominally compliant units and heat pump water heaters have air flow 

requirements not needed by electric-resistant water heaters. Additionally, HPWHs create cool air 

that could help offset the cooling load in the house if the HPWH was located inside the 

conditioned space or HPWH exhaust air was ducted into the conditioned space. 

6.1 Site Approval, National Environmental Policy Act, and DD1391 

6.1.1 Advanced Power Strip Demonstration

Site selection presented some challenges for the APS demonstration. As noted in the section summary, the 

demonstration used an “elect-in” strategy for identifying residences for participation. This approach 

required developing an awareness campaign for informing residents of the demonstration, educating them 

on the benefits, and seeking their participation. The awareness campaign required significant time for 

developing pamphlets and flyers, receiving approval by NAVFAC, NBG Housing, and NREL public 

affairs entities, and subsequently distributing information in multiple forums (e.g., email, town hall 

announcements, etc.). Although information was distributed to all NBG residents, participation in the 

demonstration remained relatively low. For future residential deployments of APS devices, it is 

recommended the best strategy for acquiring resident participation is carefully considered. An “elect-out” 

approach may yield better results. 

Site approval activities for this demonstration were minimal. DD1391 and National Environmental Policy 

Act (NEPA) evaluations were not required due to the nature of the work. 

6.1.2 Enhanced Energy Efficiency Demonstration

A minimal degree of work activity was required for EEE site selection and site approval activities. Site 

selection was guided by a short list of housing criteria, used by the NBG Housing Authority for selection 

of appropriate residences. These criteria included: 

• Minimum of two occupants 

• Representative of majority of NBG residential stock

• HVAC, water heater equipment due for an upgrade

• Water heater locations in compliance with HPWH installation requirements. 

Several residences met this criteria and final selection was accomplished without difficulty. Subsequent 

site approval and other administrative activities did not pose a significant challenge or time constraint. A 

DD1391 submittal was not required for this demonstration owing to the nature of the work.4 The NEPA 

 

4 Determination made by NAVFAC Pacific Asset Management on Jan. 09, 2013.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
48 

determination for this activity was a categorical exclusion, with its classification as a sustainment, 

restoration, and modernization project. 

6.2 Contracts and Procurement 

For the APS demonstration, APS devices were procured by NREL and delivered to the NBG residences. 

Residents then self-performed installation of the APS devices using training materials included in the 

delivered packages from NREL. 

For the EEE demonstration, a competitively selected, general service contract was awarded to Chugach 

World Services Inc. for procurement and installation of all EEE equipment. Execution of this contract was 

straightforward and no special comment is warranted.

6.3 Design 

Design activity for these demonstrations was very limited. All of the technologies demonstrated are 

standard, commercially available products. Modification or redesign of the technologies themselves was 

not considered for these demonstrations. 

A minimal amount of site design work was required for the EEE demonstration. The contractor was 

required to properly size the A/C units to the conditioned space and evaluate floor plans and physical 

space conditions for installation and plumbing of the heat pump water heaters. No site design work was 

required for the APS demonstrations, as these devices are simple “plug and play” technology offerings. 

6.4 Installation and Construction 

For the APS demonstration, devices and training materials for proper installation were shipped directly to 

the residences. The original plan was to have all residents self-install their APS, but few took the initiative 

so many APSs had to be installed by a contractor. Poor understanding of the devices or lack of motivation 

to install may be contributing factors to this problem. For future deployments, considering options for 

increasing the percentage of effective installations is recommended. Additional training materials or onsite help support may help address these issues. Because the net payback for APSs in a large deployment 

is already small (see Table 17), hiring a contractor for site-performed installations is likely costprohibitive. Additionally, for a variety of reasons, 13 installations (27%) had to be excluded from the 

analysis. This is a significant fraction of the demonstration residences, though most of the homes were 

excluded for reasons unrelated to APS installation. 

Installation activities for the EEE demonstration occurred over a four-month period. Procurement timeline 

was significant, taking over two months due to lack of local availability of HPHW and HVAC elements 

and time for environmental coatings treatment of the outdoor condenser. Actual, on-site installation 

occurred over a month. The installations were performed similar to a normal HVAC installation with no 

special circumstances or challenges.

6.5 Operation and Maintenance 

The operation and maintenance requirements of the APS and EEE equipment are essentially the same as 

standard, commercial offerings for power strips, HVAC equipment, plumbing fixtures, and hot water 

heaters. The only unique feature lies with the HPWH, which, unlike standard electric resistant units, has 

an air filter that should be inspected monthly and cleaned if necessary. Otherwise, all elements installed 

require operation and maintenance activities consistent with activities already being performed by site 

maintenance personnel at other residences.

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
49 

6.6 Training 

For the APS demonstration, training information was included in each APS delivery package to the 

residents to help in proper installation of these devices. Additionally, NREL used a local, Guamanian 

contractor to help provide technical assistance to residents to support general troubleshooting. 

Unfortunately, as noted above, several APS devices were likely not installed properly—if they were 

installed at all. Before deploying additional APS devices in a military, residential environment, evaluating 

additional options to strengthen educational awareness is recommended. 

Training for the EEE demonstration was performed on-site, at one of the residences with the installed 

EEE equipment. The field training was used to show proper operation of all installed equipment and was 

performed by the contractor. The training took less than one hour in duration and was presented to 

appropriate NBG Housing Authority staff. The residents of each EEE home were given personal training 

by the contractor after the installation at their home was complete. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
50 

7 Commercial Readiness Qualitative Assessment

7.1 Commercial Readiness of Advanced Power Strips

APSs are commercially available from many different manufacturers and vendors, and the technology 

readiness can be assessed at technology readiness level (TRL) 9. Most stores that carry power strips, 

including hardware, electronic, and big box stores also carry APSs, though the selection is usually limited. 

A much wider range of products can be found online from large retail websites like amazon.com, 

newegg.com, and smarthome.com. APS devices on the market cost between $15 and $70, but most 

options are less than $40. The price of similar capacity surge protectors is comparable, and APSs also 

have surge protection built in. Some utilities offer rebates for APSs that would offset any price difference 

in cost between an APS and a standard power strip. 

One major barrier to APS acceptance is a general lack of awareness and understanding. Few of the 

residents that signed up for the APS demonstration had ever heard of APSs, and those that had did not 

know how they worked. There are a number of different types of APSs, ranging from simple remote 

switches to automated activity monitoring devices. They are intended for different users, but those details 

are not clear from the packaging (Earle & Sparn, 2012). There is very little consumer education

surrounding APSs, and additional confusion is introduced by some stores that market power strips with 

unusual form factors (but no advanced controls) as “advanced power strips.” These obstacles led NREL to 

create a consumer guide to purchasing an APS that gives some information on how different APS work 

(see Appendix F).

Once an APS is purchased, getting it properly installed also appears to be a difficult step. In most cases, 

installing an APS means crawling behind an entertainment center or desk and untangling the mess of 

wires there. Additionally, the instructions included with the APS can be difficult to interpret—either 

because they do not contain enough detail or because they are overly detailed and long. The installation 

instructions provided by NREL (Appendix B) were created to provide simplified instructions, but they are 

specific to this demonstration. 

Lastly, expected energy savings from APS is not well known. There is significant variability between 

different households, as was seen in this demonstration, and there have not been enough large-scale 

demonstrations to establish confidence in expected savings. Northeast Energy Efficiency Partnerships 

(NEEP) published a report on expected savings for APSs that assumes all standby loads in the home 

office and home entertainment center can be saved, which results in an estimated 75 kWh/year in savings 

in a home entertainment center and about 30 kWh/year savings in a home office (NEEP Data Working 

Group, 2012). These findings are fairly consistent with this study’s results. As more field trials and 

analyses evaluate APSs and studies are conducted over longer periods to enable assessment of retention, 

confidence will grow in the expected savings. APSs present a significant potential for a low-cost solution 

to a complex problem of growing plug loads in homes. 

7.2 Commercial Readiness of Enhanced Energy Efficiency Technologies

All of the technologies included in the EEE demonstration are commercially available and can be 

assessed at TRL 9. High-efficiency air conditioners with a SEER greater than 20 are available from 

multiple manufacturers. In many climates, the more expensive, high-efficiency systems are not costeffective. However, efficiency programs like ENERGY STAR® have continued to push the airconditioning industry toward higher-efficiency products. As even better products come out, SEER 21 air 

conditioners will become cheaper and more practical for more places. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
51 

The in-line dehumidifier is somewhat unique, as it is integrated with the air conditioner and air handler, 

but there are many other ducted dehumidifiers on the market. The EEE demonstration results show newer 

air conditioners provide more latent cooling, so additional dehumidification may not be necessary. If 

additional dehumidification is desired, the standalone dehumidifiers currently installed should be 

sufficient, though quieter models would be preferred by the residents. Dehumidifiers are an additional 

piece of HVAC equipment that are not needed in many climates, but are becoming more important in 

high-efficiency homes that require less cooling. Standalone dehumidifiers are cheaper and do not require 

special installation like ducted systems, so they are more common. 

Programmable thermostats are not a new or uncommon technology, but they are underutilized in a 

different sense. A study done in 2011 found that only a third of American homes had a programmable 

thermostat and only about half the homes with a programmable thermostat actually programmed them to 

save energy during times when heating or cooling was not needed (Peffer, Pritoni, Meier, Aragon, & 

Perry, 2011). There have been well-documented barriers to programmable thermostats that are mostly 

related to their usability. New products on the market, like the Nest thermostat, aim to learn people’s 

behavior to automatically save energy. The programmable thermostat used in this demonstration has a 

smartphone app that allows people to change their thermostat remotely and allows them a more familiar 

interface to program their thermostat. These innovative features come with additional cost though, so even 

if the usability barrier is overcome, a cost barrier may exist. 

HPWHs are a relatively new technology, even though commercial products were first created in the 1950s 

(albeit with substantial problems). The most recent incarnation of the HPWH has been more successful 

than those early attempts, and the image of the technology has been improved by reputable water heater 

manufacturers producing HPWHs. HPWHs are much more efficient than electric-resistance water heaters, 

and regions of the country that have a high saturation of electric water heaters also tend to be climates that 

are well-suited to HPWH (Maguire, Burch, Merrigan, & Ong, 2013). Barriers to HPWH deployment 

include the higher cost (they are usually $800-$1,000 more expensive than a standard electric water 

heater) and lack of awareness. Some big box stores carry HPWHs, and there are sizable rebates available 

from federal and local rebate programs. Targeted marketing in the right climates may increase awareness 

and consumer acceptance. 

Low-flow shower heads are required by federal regulations and so are very common. There are no 

barriers to commercialization. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
52 

8 Recommended Next Steps

8.1 Recommended Next Steps for Advanced Power Strips

Despite the challenges of the APS demonstration, advanced power strips are a promising low-cost 

technology. The energy savings per APS is small, but so is the cost of each device. There are few options 

available to curb the ever-growing segment of plug loads in residential buildings, and APSs are a simple 

solution that can be employed in all types of residences. This technology is ready for deployment, though 

the best deployment method may depend on the situation and goals for the specific base. 

Recommendations for future APS deployment: 

• The best time to install APSs is when residents are moving into their homes, so APSs could be 

included in a move-in package. 

• If a large-scale deployment was planned in the future, the APS installation should be performed by 

a third party to ensure the devices are installed and installed properly. This would add to the cost 

of the deployment, but the savings number may be better because the installation of the APS 

would be guaranteed. 

• The net cost savings in Table 17 show that a larger deployment would result in positive savings, 

so the bigger the deployment, the better. 

• Lack of education is a large barrier with APSs, so awareness or training activities could be used to 

help educate people about how to install and use an APS, and its energy savings benefits. 

• Children are often more tech-savvy than their parents. At least one home in the demonstration was 

signed up by the family’s middle school-aged daughter. Tapping into the interest of children and 

teenagers may be a good way to bridge education and energy efficiency. 

• Especially on bases where residents pay their electricity bill, stocking APSs in the on-base Navy 

Exchange store may encourage the more energy-conscious residents to invest in an APS, 

especially if copies of the consumer education flyer (Appendix F) developed by NREL were 

available as well. Another option would be to provide residents with a small coupon for the APS 

models available at the Naval Exchange. Having the residents purchase the APS may also improve 

installation rates as people would be personally invested. 

Lessons learned with the APS demonstration: 

• No matter how enthusiastic a resident may be, the effort required to install APS on their own is 

usually too much. 

• Once installed, residents are generally willing to adapt their habits. 

• People seemed more concerned with the monitoring part of the demonstration than actually using 

the APS. Several of our participants uninstalled their monitoring equipment before the APSs were 

installed, for no obvious reason. 

8.2 Recommended Next Steps for Enhanced Energy Efficiency

Technologies

When NBG housing air conditioners and water heaters reach the end of their lives, they should be 

replaced with SEER 21 air conditioners and heat pump water heaters. NBG is already following NREL

recommendations for next steps by updating the current standards to specify energy efficient technology. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
53 

This will ensure new homes and existing homes in need of new appliances or large equipment will receive 

energy efficient products. 

The technologies included in the EEE demonstration had a significant impact on the houses’ energy 

consumption, while maintaining comfort and user satisfaction. The only exception was the in-line 

dehumidifier that did not have a measurable impact on the indoor air conditions. High-efficiency air 

conditioners and HPWHs have already been integrated into plans for future upgrades on Naval Base 

Guam. The standard for all new water heaters was previously changed to solar thermal water heaters 

(found in all new homes in the North Tipalao neighborhood), but they have since changed that standard to 

mandate HPWHs instead. HPWHs are much cheaper than solar water heaters, especially when solar water 

heaters have to be protected in hurricane/typhoon prone areas, and they still provide significant energy 

savings. 

A follow-on project currently underway will outfit 20 additional homes with the energy efficiency 

technologies from the EEE demonstration (excluding the in-line dehumidifier) in the Lockwood Terrace 

and Apra View neighborhoods on NBG. One difference in these installations is the water heater is located 

inside the conditioned space, in the laundry room, in the Apra View homes, so this will be a good 

opportunity to see if the same magnitude of energy savings is achieved and if user satisfaction is 

maintained for conditioned space installations. 

There may be opportunities for further education on technology like programmable thermostats. Few 

people had used the scheduling feature of their programmable thermostat, which provides an opportunity 

for further energy savings. If there are people at home during the day, there is less opportunity to set a 

daily schedule. Education about the features and benefits of programmable thermostats may help those on 

base that can set up their thermostat during the day to save energy. 

These recommendations are generally restricted to Guam, as the warm climate and high electricity prices 

lead to short payback periods for high-efficiency equipment. Even a climate like Hawaii may be mild 

enough to require a change in the recommendations from this demonstration. Even if the 

recommendations are specific to Guam, there are opportunities to work with the rest of Guam to inform 

the public of their options and the cost/benefit trade-offs for these energy efficient technologies. HPWHs 

are a technology that Guamanians are interested in but had no experience with. This demonstration may 

encourage more people on the island to invest in better technology in their own homes. 

Lessons learned with the EEE demonstration: 

• People are generally impressed by the look of new technology, even if they do not understand it. 

• Noise may trump other comfort concerns, like humidity. Every single resident said they were 

happy with the new air conditioner because it was quieter. On the other hand, a few people noted 

they turned off their standalone dehumidifiers because they were too loud. 

• BEopt can be used to define similar packages of energy-efficient and cost-effective retrofit 

measures for any home in any climate. Major retrofit efforts in other climates can use this tool to 

select a package of measures, including an estimate of predicted energy savings. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
54 

References

ASHRAE. "Thermal Environmental Conditions for Human Occupancy." ANSI/ASHRAE Standard 55-

2010, 2010. 

Christensen, C., R. Anderson, S. Horowitz, A. Courtney, and J. Spencer. BEopt Software for Building 

Energy Optimization: Features and Capabilities. Golden, CO: National Renewable Energy 

Laboratory, 2006. 

Earle, L., and B. Sparn. "Results of Laboratory Testing of Advanced Power Strips." ACEEE Summer 

Study Proceedings, 2012. 

Maguire, J., J. Burch, T. Merrigan, and S. Ong. Energy Savings and Breakeven Cost for Residential Heat 

Pump Water Heaters in the United States. TP-5500-58594, Golden, CO: National Renewable 

Energy Laboratory, 2013. 

NEEP Data Working Group. Advanced Power Strips Deemed Savings Methodology. Northeast Energy 

Efficiency Partnerships, 2012. 

NOAA. Quality Controlled Local Climatological Data. 2013. http://cdo.ncdc.noaa.gov/qclcd. 

Peffer, T., M. Pritoni, A. Meier, C. Aragon, and D. Perry. "How people use thermostats in homes: A 

review." Building and Environment 46 (2011): 2529-2541. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
55 

Appendix A: Advanced Power Strip Fact Sheet

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
56 

Appendix B: Advanced Power Strip Installation Instructions

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
57 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
58 

Appendix C: Advanced Power Strip Pre- and PostDemonstration Surveys

Advanced Power Strips: Pre-Demonstration Questions

Home Entertainment Area:

Is there a power strip already in use? How 

many, if more than one? 

List the devices connected to the TV. 

How many hours per day is the 

entertainment center typically used during 

the week?

How many hours per day is the 

entertainment center typically used on the 

weekend?

Home Office Area:

Is there a home office area (designated 

space for computer and peripherals to be 

plugged in)? 

Is there a power strip already in use? How 

many, if more than one? 

List the devices connected to the computer. 

Is the computer a desktop or laptop? 

How many hours per day is the home office 

typically used during the week?

How many hours per day is the home office 

typically used on the weekend? 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
59 

Advanced Power Strips: Post-Demonstration Questions

1. Which APS did you have installed—home entertainment, home office, or both?

2. Did you have any trouble setting up the home entertainment APS? Were the instructions unclear? 

What could be done to improve instructions? 

3. What did you think of the home entertainment APS? Did you notice its control features? 

4. Did you uninstall the home entertainment center APS during the study? Do you plan to uninstall it 

now that the demonstration is over? 

5. Did you have any trouble setting up the home office APS? Were the instructions unclear? What 

could be done to improve instructions? 

6. What did you think of the home office APS? Did you notice its control features? 

7. Did you uninstall the home office APS during the study? Do you plan to uninstall it now that the 

demonstration is over? 

8. If you were paying your utility bills, would you buy a similar product in the future? Why or why 

not? 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
60 

Appendix D: Enhanced Energy Efficiency PostDemonstration Survey

Enhanced Energy Efficiency: Post Demonstration Questions

1. What was your general impression of the new equipment installed in your house? 

2. Did you notice any effects of the new air conditioner—improved or worsened comfort, more or 

less noise, longer or shorter run times? 

3. Did your home have a new dehumidifier installed? If so, did you notice any change to the indoor 

air conditions? Did it feel less humid?

4. What did you think of the programmable thermostat? Did you set up a daily schedule? What 

temperature (and humidity, if applicable) settings did you use? Did you ever use the smartphone 

app to change the set point remotely?

5. Did you notice the effect of the low-flow shower heads? Would you install low-flow shower heads 

in your home in the future? 

6. Did you notice any effects of the new water heater—more or less available hot water, too noisy, 

more or less comfortable garage (if applicable)? Did you change the operating mode or set point to 

improve the amount of hot water available? What did you set the operating mode and set point to? 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
61 

Appendix E: Economic Analysis for Advanced Power Strip

and Enhanced Energy Efficiency Demonstrations

Cost Information

Cost Assumptions for Minimally Efficient Retrofit

To evaluate the economic benefit of the enhanced energy efficiency (EEE) retrofits, pricing was estimated 

for a hypothetical, minimally efficient retrofit (lowest cost and minimum efficiency performance) for a 

comparative analysis. The following factors were used as the basis of estimate for the pricing of the 

minimally efficient retrofit. 

• Equipment selection was based on the key technical specifications (tonnage, energy efficiency 

ratio (EER), tank size, etc.) of the equipment existing at each residence prior to the demonstration, 

which was replaced by the EEE retrofits.

• Equipment pricing was performed by identifying the lowest cost option meeting the equipment 

technical specifications, as presented by the US. General Services Administration’s “GSA 

Advantage! Online Shopping” website.

5 See Table A-1 for the unburdened equipment pricing 

used. 

• Design activities were considered minimal and of equivalent cost to those required for the EEE 

retrofits (design activities focused on appropriate sizing of the HVAC systems). No special design 

costs are believe needed for the EEE retrofits relative to a standard installation of commercial 

products. 

• Aggregate installation costs were estimated at 95% of realized costs for EEE retrofit installation. 

The price reduction of 5% was applied to account for the added complexity of the HPWH 

installation versus a standard, electric-resistant hot water heater. 

Table A-1. Estimated, Unburdened Equipment Pricing for the Minimally Efficient Retrofits

Summary Breakout of Equipment Costs

Item # Item Units Unit Price

1 Electric-Resistant Water Heater (40 gallons) 8 $240

2 Shower Head 16 $54

3 A/C Unit (SEER 13, 4 ton) (AHU, Condenser) 8 $2,100

4 Thermostat 8 $16

5 Standalone Dehumidifier (30–40 pint/day) 8 $200

Economic Analysis Information

Energy Return on Investment Analyses

Table A-2 provides a summary of key information regarding the energy return on investment (eROI) 

analyses developed for the EEE project.

 

5 The GSA Advantage! Online Shopping website can be found at: www.gsaadvantage.gov/advantage/main/start_page.do. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
62 

Table A-2. Key Information Regarding eROI Analyses Performed for this Report

eROI Analyses: Key Information

Input Type EEE Demo APS Demo

Date of Analysis Nov. 18, 2013 July 16, 2013

eROI Version v.2.9.16 v2.9.16B

Project Overview Tab 

 Project Category Facility En. Impr. Facility En. Impr.

 Regional Priority Project No No

Max. Financial Benefits Tab 

 Salvage Value $0 $0 

Provide Reliable Energy Tab 

 MDI Critical Facilities 0 0 

Regulatory and SH Expect. Tab 

 Regulatory Compliance 2 2 

 Public Perception 0 0 

 Quality of Service, Goals 1 0 

 Quality of Service, # People 2 2 

Develop. Enabling Infrast. Tab 

 Question 1, Data Improvement 3 2 

 Question 2, Flex. Energy Inf. 0 1 

 Question 3a, Energy Indep. 3 2 

 Question 3b, % of Installations 50% 25%

Project Risk Tab 

 1. Timeline and Cost +/- 10% +/- 10%

 2. Energy Reduction +/- 10% +/- 10%

 3a. Facility Energy Reliance +/- 10% +/- 10%

 3b. Facility Outages +/- 10% +/- 10%

 3c. Backup Power +/- 10% +/- 10%

 4. Regulatory and Stakeholders +/- 10% +/- 10%

 5. Enabling Infrastructure +/- 10% +/- 10%

 6. Aggregate Benefits +/- 25% +/- 10%

Impact of Deferring Tab 

 Impact of Deferring One Year 0% Loss 0% Loss

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
63 

Building Life-Cycle Cost Analyses

Table A-3 provides a summary of key information regarding the Building Life-Cycle Cost (BLCC) 

analyses developed for this project.

Table A-3. Key Information Regarding BLCC Analyses Performed for this Report

BLCC Analyses: Key Information

Input Type Value

Report Type MilCon

BLCC Version 5.3

Location Hawaiia 

Discounting Convention Mid-Year

Analysis Type Constant Dollars

Base Date Oct. 2013

Beneficial Occupancy Oct. 2013

Length of Study 10 Years

Energy Usage Indice 100% throughout economic life

Investment Cost, Cost-Phasing 0%

Energy Escalation Factor 0%

a Guam is not available in BLCC. 

Table A-4 provides a summary of key information regarding the BLCC analyses developed for the advanced 

power strip project.

Table A-4. Key Information Regarding BLCC Analyses Performed for this Report

BLCC Analyses: Key Information

Input Type Value

Report Type MilCon

BLCC Version 5.3

Location Hawaiia 

Discounting Convention Mid-Year

Analysis Type Constant Dollars

Base Date Oct. 2013

Beneficial Occupancy Oct. 2013

Length of Study 4 Years

Energy Usage Indice, 1st Year 100% Usage

Energy Usage Indice, 2nd Year 75% Usage

Investment Cost, Cost-Phasing 0%

Energy Escalation Factor 0%

a Guam is not available in BLCC. 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
64 

Appendix F: Consumer Guide for Advanced Power Strips

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.
65 

This report is available at no cost from the National Renewable Energy Laboratory (NREL) at www.nrel.gov/publications.