Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

2010 EGU MACT ICR - CIPCO Fair#2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, January 22, 2011 Page 1 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Facility Information:

Fair Station

3800 Highway 22

Muscatine IA

Contact: Sam Stineman

Phone: 319-366-8011

Fax: 319-366-6328

Email: sam.stineman@cipco.net

Testing Company:

Platt Environmental

1520 Kensington Road

Suite 204

Oak Brook IL 60523-2141

Contact:Eric Ehlers

Phone: 630-521-9400

Fax: 630-521-9494

Email: EEhlers@plattenv.com

Air Permit Number:

1218

Permitted Source ID/Name:

2 Fair Station Unit 2

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

36,0000 lb/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Fair Station Unit 2 is a wall fired, dry bottom pulverized coal fired boiler capable of approximately 500mmBTU/hr. 

All fuel at the facility comes from Illinois Basin mines and is bituminous. The unit has an electrostatic precipitator to 

control particulate and low NOx burners.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: CIPCO Fair Station FRS #: 110028167702

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 78 0 0 0 0 0 4 1

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Regulation Description Compound Limit Unit

Acid Rain Program (Calendar Year Average) Nitrogen oxides (NOx) 0.46 lb/million BTU 

using CO2

Title V - Particulate Matter Total Particulate 0.43 lb/million BTU 

using CO2

Title V - SO2 Sulfur Dioxide 6 lb/million BTU 

using CO2

Saturday, January 22, 2011 Page 2 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Stack Exit Formaldehyde Method 0011 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Stack Exit Total PCBs Method 23 3 480 0

Stack Exit Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Saturday, January 22, 2011 Page 3 of 28
2010 EGU MACT ICR - CIPCO Fair#2

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

There were no modifications or deviations to test methods.

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Cobalt Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit Co2 Method 3A CO2 3 240 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Filterable Particulate Method 5 3 240 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Saturday, January 22, 2011 Page 4 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Sampling / Stack Data Results Summary

Location Stack Exit - Method 0011

Average

Run Number M0011-1 M0011-2 M0011-3

Test Date 8/6/2010 8/6/2010 8/6/2010

Run Start Time 7:20:00 AM 9:55:00 

AM

12:25:00 PM

Run Finish Time 9:27:00 AM 12:07:00 

PM

2:32:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 90.312 88.405 87.661 88.793

Moisture Content of Stack Gas, % 8.15 8.27 8.53 8.317

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.6 13.4 13.4 13.467

Oxygen, % 5.6 5.7 5.7 5.667

Average Stack Gas Temperature, °F 333.88 340.79 342.83 339.167

Dry Volumetric Flow Rate, dry scfm 106,175.6 103,255.3 102,228.0 103,886.300

Actual Wet Volumetric Flue Gas Flow Rate, acfm 176,042.5 172,916.6 172,120.2 173,693.100

Percent Isokinetic of Sampling Rate, % 96.9 97.5 97.7 97.367

F-Factor, dscfm/MMBtu @ %O2 9499 9567 9736 9,600.667

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, January 22, 2011 Page 5 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Saturday, January 22, 2011 Page 6 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, January 22, 2011 Page 7 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, January 22, 2011 Page 8 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, January 22, 2011 Page 9 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Saturday, January 22, 2011 Page 10 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Emissions Summary

Location: Stack Exit - Method 0011

Compound: Formaldehyde

Average

RunNumber M0011-1 M0011-2 M0011-3

Mass_mg 0.057 0.047 0.009 0.038

lb/mmBtuO2 1.81E-05 1.54E-05 3.03E-06 0.000

ppm 1.79E-02 1.50E-02 2.90E-03 0.012

ppm@7%O2 1.63E-02 1.37E-02 2.65E-03 0.011

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 1.11E-02 1.10E-02 1.15E-02 0.011

ppm 1.18E+01 1.15E+01 1.18E+01 11.700

ppm@7%O2 1.07E+01 1.05E+01 1.08E+01 10.667

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 2.49E-03 1.53E-03 2.28E-03 0.002

ppm 1.68E+00 1.02E+00 1.49E+00 1.397

ppm@7%O2 1.53E+00 9.33E-01 1.36E+00 1.274

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 630 620 590 613.333

lb/mmBtuO2 1.86E-01 1.78E-01 1.70E-01 0.178

Compound: Hydrogen Fluoride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 15 15 19 16.333

lb/mmBtuO2 4.42E-03 4.30E-03 5.48E-03 0.005

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.008 0.0147 0.0147 0.012

lb/mmBtuO2 1.32E-06 2.73E-06 2.80E-06 0.000

Compound: Arsenic

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.1132 0.2099 0.2254 0.183

Saturday, January 22, 2011 Page 11 of 28
2010 EGU MACT ICR - CIPCO Fair#2

lb/mmBtuO2 1.87E-05 3.89E-05 4.29E-05 0.000

Compound: Beryllium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00276 0.00684 0.00724 0.006

lb/mmBtuO2 4.56E-07 1.27E-06 1.38E-06 0.000

Compound: Cadmium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.002 0.00264 0.012 0.006

lb/mmBtuO2 3.30E-07 4.90E-07 2.28E-06 0.000

Compound: Chromium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.13093 1.57261 0.45551 0.720

lb/mmBtuO2 2.16E-05 2.92E-04 8.67E-05 0.000

Compound: Cobalt

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00868 0.039 0.0333 0.027

lb/mmBtuO2 1.43E-06 7.23E-06 6.34E-06 0.000

Compound: Filterable Particulate

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 229.3 306.2 375.1 303.533

lb/mmBtuO2 3.79E-02 5.68E-02 7.14E-02 0.055

Compound: Lead

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.03252 0.09378 0.10212 0.076

lb/mmBtuO2 5.37E-06 1.74E-05 1.94E-05 0.000

Compound: Manganese

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.04216 0.149 0.11846 0.103

lb/mmBtuO2 6.96E-06 2.76E-05 2.25E-05 0.000

Compound: Nickel

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0802 0.9322 0.4039 0.472

lb/mmBtuO2 1.32E-05 1.73E-04 7.69E-05 0.000

Compound: Selenium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.2362 0.2182 0.2282 0.228

Saturday, January 22, 2011 Page 12 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Process Run Data

lb/mmBtuO2 3.90E-05 4.05E-05 4.34E-05 0.000

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3

Mass_mg 77.5 495.8 395.2 322.833

lb/mmBtuO2 1.69E-02 1.15E-01 8.90E-02 0.074

Compound: Filterable PM2.5

Average

RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3

Mass_mg 52.7 304 134.5 163.733

lb/mmBtuO2 1.15E-02 7.08E-02 3.03E-02 0.038

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3

Mass_mg 288.4 401.2 611.2 433.600

lb/mmBtuO2 6.28E-02 9.34E-02 1.38E-01 0.098

Compound: Organic Condensible Particulate

Average

RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3

Mass_mg 40.6 24.1 8.4 24.367

lb/mmBtuO2 8.84E-03 5.61E-03 1.89E-03 0.005

Compound: Total Particulate

Average

RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3

Mass_mg 406.5 921.1 1014.8 780.800

lb/mmBtuO2 8.85E-02 2.14E-01 2.29E-01 0.177

Compound: Total PM2.5

Average

RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3

Mass_mg 381.7 729.3 754.1 621.700

lb/mmBtuO2 8.31E-02 1.70E-01 1.70E-01 0.141

Saturday, January 22, 2011 Page 13 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Coal Firing Rate 35800 lb/hr Run 1 - OTM 

27/28, M5/29, 

M30B

36000

1 Average Heat Input 441 MMBtu/hr Run 1 - OTM 

27/28, M5/29, 

M30B

430

1 Steam Output 336 1000 lb steam/hr Run 1 - OTM 

27/28, M5/29, 

M30B

330

1 Unit Gross Electrical Output 37.8 MW Run 1 - OTM 

27/28, M5/29, 

M30B

37

2 Coal Firing Rate 37500 lb/hr Run 2 - OTM 

27/28, M5/29, 

M30B

36000

2 Average Heat Input 442 MMBtu/hr Run 2 - OTM 

27/28, M5/29, 

M30B

430

2 Steam Output 339 1000 lb steam/hr Run 2 - OTM 

27/28, M5/29, 

M30B

330

2 Unit Gross Electrical Output 37.9 MW Run 2 - OTM 

27/28, M5/29, 

M30B

37

3 Coal Firing Rate 37500 lb/hr Run 3 - OTM 

27/28, M5/29, 

M30B

36000

3 Average Heat Input 440 MMBtu/hr Run 3 - OTM 

27/28, M5/29, 

M30B

430

3 Steam Output 334 1000 lb steam/hr Run 3 - OTM 

27/28, M5/29, 

M30B

330

3 Unit Gross Electrical Output 37.5 MW Run 3 - OTM 

27/28, M5/29, 

M30B

37

4 Coal Firing Rate 36400 lb/hr Run 1 - M26A, 

CTM033

36000

4 Average Heat Input 461 MMBtu/hr Run 1 - M26A, 

CTM033

430

4 Steam Output 339 1000 lb steam/hr Run 1 - M26A, 

CTM033

330

4 Unit Gross Electrical Output 37.8 MW Run 1 - M26A, 

CTM033

37

Saturday, January 22, 2011 Page 14 of 28
2010 EGU MACT ICR - CIPCO Fair#2

5 Coal Firing Rate 39200 lb/hr Run 2 - M26A, 

CTM033

36000

5 Average Heat Input 462 MMBtu/hr Run 2 - M26A, 

CTM033

430

5 Steam Output 340 1000 lb steam/hr Run 2 - M26A, 

CTM033

330

5 Unit Gross Electrical Output 37.9 MW Run 2 - M26A, 

CTM033

37

6 Coal Firing Rate 36700 lb/hr Run 3 - M26A, 

CTM033

36000

6 Average Heat Input 460 MMBtu/hr Run 3 - M26A, 

CTM033

430

6 Steam Output 336 1000 lb steam/hr Run 3 - M26A, 

CTM033

330

6 Unit Gross Electrical Output 37.6 MW Run 3 - M26A, 

CTM033

37

7 Coal Firing Rate 37100 lb/hr Run 1 - M0010, 

M0031, M0011, 

M10, M25/18

36000

7 Average Heat Input 454 MMBtu/hr Run 1 - M0010, 

M0031, M0011, 

M10, M25/18

430

7 Steam Output 333 1000 lb steam/hr Run 1 - M0010, 

M0031, M0011, 

M10, M25/18

330

7 Unit Gross Electrical Output 37.6 MW Run 1 - M0010, 

M0031, M0011, 

M10, M25/18

37

8 Coal Firing Rate 37100 lb/hr Run 2 - M0010, 

M0031, M0011, 

M10, M25/18

36000

8 Average Heat Input 464 MMBtu/hr Run 2 - M0010, 

M0031, M0011, 

M10, M25/18

430

8 Steam Output 335 1000 lb steam/hr Run 2 - M0010, 

M0031, M0011, 

M10, M25/18

330

8 Unit Gross Electrical Output 37.7 MW Run 2 - M0010, 

M0031, M0011, 

M10, M25/18

37

9 Coal Firing Rate 36700 lb/hr Run 3 - M0010, 

M0031, M0011, 

M10, M25/18

36000

9 Average Heat Input 464 MMBtu/hr Run 3 - M0010, 

M0031, M0011, 

M10, M25/18

430

Saturday, January 22, 2011 Page 15 of 28
2010 EGU MACT ICR - CIPCO Fair#2

APCD Run Data

Process Lab Run Data

9 Steam Output 335 1000 lb steam/hr Run 3 - M0010, 

M0031, M0011, 

M10, M25/18

330

9 Unit Gross Electrical Output 37.7 MW Run 3 - M0010, 

M0031, M0011, 

M10, M25/18

37

Run Name Value UOM Comments

Target

Value

LOW NOX BURNERS lb/mmBTU 0.46

ELECTROSTATIC PRECIPITATOR lb/mmBTU 0.43

Run Name Value UOM Comments

1 See Comments. 0

Saturday, January 22, 2011 Page 16 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Sampling / Stack Data Results Detail

Location Stack Exit - Method 0011

Average

Run Number M0011-1 M0011-2 M0011-3

Test Date 8/6/2010 8/6/2010 8/6/2010

Run Start Time 7:20:00 AM 9:55:00 AM 12:25:00 PM

Run Finish Time 9:27:00 AM 12:07:00 PM 2:32:00 PM

Net Traversing Points 28 28 28

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.211 0.211 0.211 0.211

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.003 1.003 1.003 1.003

Barometric Pressure, inches of Mercury 29.5 29.5 29.5 29.500

Average Orifice Meter Differential, inches H2O 1.63 1.53 1.54 1.567

Dry Gas Meter Volume Sampled, cubic feet 92.620 92.500 91.540 92.220

Average Dry Gas Meter Temperature, °F 77.67 88.42 87.35 84.480

Dry Gas Meter Volume Sampled, dscf 90.312 88.405 87.661 88.793

Total Moisture Liquid collected, g 170.1 169.3 173.5 170.967

Volume of Water Vapor, standard cubic feet 8.01 7.97 8.17 8.050

Moisture Content of Stack Gas, % 8.15 8.27 8.53 8.317

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9185 0.9173 0.9147 0.917

Carbon Dioxide, % 13.6 13.4 13.4 13.467

Oxygen, % 5.6 5.7 5.7 5.667

Carbon Monoxide & Nitrogen, % 80.8 80.9 80.9 80.867

Fuel Factor 1.13 1.13 1.13

Dry Molecular Weight, lb/lb-Mole 30.40 30.37 30.37 30.380

Wet Molecular weight, lb/lb-Mole 29.39 29.35 29.31 29.350

Flue Gas Static Pressure, inches of H2O 0.5 0.5 0.5 0.500

Absolute Flue Gas Pressure, inches of Mercury 29.54 29.54 29.54 29.540

Average Stack Gas Temperature, °F 333.88 340.79 342.83 339.167

Average Velocity Head, inches of H2O 1.6578904574

2867

1.583712666

25913

1.562967744

07957

1.602

Average Stack Gas Velocity, feet/second 88.42 86.85 86.45 87.240

Stack Cross-Sectional Area, square feet 33.183 33.183 33.183 33.183

Dry Volumetric Flow Rate, dry scfm 106,175.6 103,255.3 102,228.0 103,886.300

Actual Wet Volumetric Flue Gas Flow Rate, acfm 176,042.5 172,916.6 172,120.2 173,693.100

Percent Isokinetic of Sampling Rate, % 96.9 97.5 97.7 97.367

Percent Excess Air, % 35.6 36.4 36.4 36.133

F-Factor, dscfm/MMBtu @ %O2 9499 9567 9736 9,600.667

Round Duct Diameter, inches 78 78 78

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Saturday, January 22, 2011 Page 17 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 18 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 19 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, January 22, 2011 Page 20 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, January 22, 2011 Page 21 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 22 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 23 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 24 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 25 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 26 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 27 of 28
2010 EGU MACT ICR - CIPCO Fair#2

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, January 22, 2011 Page 28 of 28