Name: Phillip J Yates

Title: Production Manager

Company: FPL

Sign Date: 6/25/2010

Name: Thomas K. Graham

Title: Director of Operations

Company: Air Hygiene International, Inc.

Sign Date: 6/9/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Martin Energy Center, Unit #1, Information Collection Request

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 15, 2011 Page 1 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Facility Information:

Martin Energy Center

21900 SW Warfield Boulevard, SR 710

Indiantown FL 34956

Contact: Augie De La Vega

Phone: (305) 242-3896

Fax:

Email: augie.de.la.vega@fpl.com

Testing Company:

Air Hygiene International, Inc.

5634 S. 122nd East Ave, Suite F

Tulsa OK 74146

Contact:Thomas Graham

Phone: (918) 307-8865

Fax: (918) 307-9131

Email: tom@airhygiene.com

Air Permit Number:

0850001-018-AV

Permitted Source ID/Name:

PMR1 Foster Wheeler, Wall Fired Boiler

Permitted Maximum Process Rate:

863.3 MW

Max. Normal Operation Process Rate:

800 MW

Target Process Test Rate

800 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster 

Wheeler design, designated as Units PMR1 and PMR2. The facility is located at 21900 Southwest Warfield 

Boulevard, State Route 710 in Indiantown, Florida. Unit PMR1 and PMR2 are of identical design and consists of 

two wall fired boilers and ancillary equipment designed to generate 863.3 megawatts (MW) of electricity each with 

rated heat inputs of 8,650 million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). 

Fuel oil consumption is rated at 600,000 pounds per hour. Unit PMR1 and PMR2 utilize low nitrogen oxide (NOx) 

burner technology to control NOx emissions and cyclone separators to control particulate matter (PM) emissions. 

Emission testing will be conducted from platforms on the independent stacks of each unit.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 0850001 FRS #: 110008320566

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

PMR1 - D/F 357.4 0 0 0 4524 876 4 24

PMR1 - Gases 357.4 0 0 0 4524 876 4 1

PMR1 - Metals 357.4 0 0 0 4524 876 4 24

PMR1 - PM 357.4 0 0 0 4524 876 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Regulation Description Compound Limit Unit

Not applicable.

Tuesday, February 15, 2011 Page 2 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

PMR1 - D/F % H2O Method 1 - 4 3 480 24

PMR1 - D/F 2,3,7,8-TCDD Method 23 3 480 24

PMR1 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 24

PMR1 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 24

PMR1 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 24

PMR1 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 24

PMR1 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 24

PMR1 - D/F OCDD Method 23 3 480 24

PMR1 - D/F 2,3,7,8-TCDF Method 23 3 480 24

PMR1 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 24

PMR1 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 24

PMR1 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 24

PMR1 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 24

PMR1 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 24

PMR1 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 24

PMR1 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 24

PMR1 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 24

PMR1 - D/F OCDF Method 23 3 480 24

PMR1 - D/F Total Dioxins Method 23 3 480 24

PMR1 - D/F Total Furans Method 23 3 480 24

PMR1 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 24

PMR1 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 24

PMR1 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 24

PMR1 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 24

PMR1 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 24

PMR1 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 24

PMR1 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 24

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

PMR1 - D/F Method 23 3 480 24

PMR1 - D/F 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 24

PMR1 - D/F 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 24

2,3,3',4,4',5,5'-HpCB 

(PCB189)

PMR1 - D/F Method 23 3 480 24

PMR1 - D/F O2 Method 3A O2 3 480 24

PMR1 - D/F Co2 Method 3A CO2 3 480 24

% H2O Method 1 - 4 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

O2 Method 3A O2 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

Co2 Method 3A CO2 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after 

initial stratification test

PMR1 - Gases

PMR1 - Metals% H2O Method 1 - 4 3 240 24

PMR1 - MetalsSelenium Method 29 3 240 24

PMR1 - MetalsManganese Method 29 3 240 24

Tuesday, February 15, 2011 Page 3 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

PM Run All - reduced to 2 hour runs to avoid high vacuum, did not pull required volumes.
PM Run 1 - oily 

substance in organic backhalf.

PMR1 - MetalsLead Method 29 3 240 24

PMR1 - MetalsFilterable Particulate Method 29 3 240 24

PMR1 - MetalsCobalt Method 29 3 240 24

PMR1 - MetalsCadmium Method 29 3 240 24

PMR1 - MetalsChromium Method 29 3 240 24

PMR1 - MetalsNickel Method 29 3 240 24

PMR1 - MetalsCo2 Method 3A CO2 3 240 24

PMR1 - MetalsO2 Method 3A O2 3 240 24

% H2O Method 1 - 4 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Organic Condensible 

Particulate

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

O2 Method 3A O2 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based 

on method calculations

PMR1 - PM

Tuesday, February 15, 2011 Page 4 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Sampling / Stack Data Results Summary

Location PMR1 - D/F - Method 23

Average

Run Number PMR1-23-1 PMR1-23-

2

PMR1-23-3

Test Date 4/6/2010 4/7/2010 4/8/2010

Run Start Time 9:15:00 AM 2:15:00 PM 11:48:00 AM

Run Finish Time 5:15:00 PM 10:15:00 

PM

7:48:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 342.102 316.770 317.751 325.541

Moisture Content of Stack Gas, % 8.97 10.18 9.37 9.507

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.03 13.01 13.11 13.050

Oxygen, % 4.58 4.5 4.55 4.543

Average Stack Gas Temperature, °F 338.50 342.96 348.75 343.403

Dry Volumetric Flow Rate, dry scfm 1,506,480.3 1,366,774.5 1,384,716.8 1,419,323.86

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,475,461.1 2,314,108.9 2,344,205.7 2,377,925.23

3

Percent Isokinetic of Sampling Rate, % 96.7 98.7 97.7 97.700

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR1 - Gases - Method 10

Average

Run Number 1-CO-1 1-CO-2 1-CO-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 

PM

4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 5 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 25A

Average

Run Number 1-THC-1 1-THC-2 1-THC-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 

PM

4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR1 - Gases - Method 3A CO2

Average

Run Number 1-CO2-1 1-CO2-2 1-CO2-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 

PM

4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 6 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 3A O2

Average

Run Number 1-O2-1 1-O2-2 1-O2-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 

PM

4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR1 - Gases - Method 6C

Average

Run Number 1-SO2-1 1-SO2-2 1-SO2-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 

PM

4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 7 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 7E

Average

Run Number 1-NOx-1 1-NOx-2 1-NOx-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 

PM

4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR1 - Metals - Method 29

Average

Run Number PMR1-29-1 PMR1-29-

2

PMR1-29-3

Test Date 4/7/2010 4/8/2010 4/8/2010

Run Start Time 2:32:00 PM 8:32:00 

AM

5:31:00 PM

Run Finish Time 6:32:00 PM 12:32:00 

PM

9:31:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 154.179 156.378 148.957 153.171

Moisture Content of Stack Gas, % 10.20 10.40 10.36 10.320

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.01 13.11 13.11 13.077

Oxygen, % 4.5 4.55 4.55 4.533

Average Stack Gas Temperature, °F 346.67 342.79 347.92 345.793

Dry Volumetric Flow Rate, dry scfm 1,350,111.9 1,340,540.0 1,258,404.8 1,316,352.23

3

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,296,970.4 2,283,176.1 2,158,190.8 2,246,112.43

3

Percent Isokinetic of Sampling Rate, % 97.2 99.3 100.8 99.100

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 8 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - PM - OTM - 27/28

Average

Run Number PMR1-

27/28-1

PMR1-

27/28-2

PMR1-

27/28-3

Test Date 4/7/2010 4/8/2010 4/9/2010

Run Start Time 8:43:00 AM 2:12:00 PM 9:49:00 AM

Run Finish Time 1:00:00 PM 5:06:00 PM 12:37:00 PM

Net Run Time, minutes 123 124 125

Dry Gas Meter Volume Sampled, dscf 40.193 42.821 41.633 41.549

Moisture Content of Stack Gas, % 9.17 9.14 9.20 9.170

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.01 13.11 13.11 13.077

Oxygen, % 4.5 4.55 4.55 4.533

Average Stack Gas Temperature, °F 338.25 350.67 346.17 345.030

Dry Volumetric Flow Rate, dry scfm 1,419,597.7 1,364,555.3 1,384,838.9 1,389,663.96

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,337,099.5 2,312,018.8 2,339,607.6 2,329,575.30

0

Percent Isokinetic of Sampling Rate, % 99.4 109.3 103.8 104.167

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 9 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Emissions Summary

Location: PMR1 - D/F - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000052 0.000000008 0.0000000031 0.000

lb/mmBtuO2 3.94E-13 6.52E-13 2.53E-13 0.000

ng/dscm 5.37E-04 8.92E-04 3.45E-04 0.001

ng/dscm@7%O2 4.57E-04 7.56E-04 2.93E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000000648 0.0000000074 0.00000000405 0.000

lb/mmBtuO2 4.91E-13 6.03E-13 3.30E-13 0.000

ng/dscm 6.69E-04 8.25E-04 4.50E-04 0.001

ng/dscm@7%O2 5.70E-04 6.99E-04 3.83E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000039 0.000000003 0.0000000021 0.000

lb/mmBtuO2 2.96E-13 2.45E-13 1.71E-13 0.000

ng/dscm 4.03E-04 3.35E-04 2.33E-04 0.000

ng/dscm@7%O2 3.43E-04 2.84E-04 1.98E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000015 0.000000002 0.0000000014 0.000

lb/mmBtuO2 1.14E-13 1.63E-13 1.14E-13 0.000

ng/dscm 1.55E-04 2.23E-04 1.56E-04 0.000

ng/dscm@7%O2 1.32E-04 1.89E-04 1.33E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000015 0.0000000038 0.0000000012 0.000

lb/mmBtuO2 1.14E-13 3.10E-13 9.78E-14 0.000

ng/dscm 1.55E-04 4.24E-04 1.33E-04 0.000

ng/dscm@7%O2 1.32E-04 3.59E-04 1.13E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000032 0.00000000259 0.0000000023 0.000

lb/mmBtuO2 2.43E-13 2.11E-13 1.87E-13 0.000

ng/dscm 3.30E-04 2.89E-04 2.56E-04 0.000

ng/dscm@7%O2 2.81E-04 2.45E-04 2.18E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Tuesday, February 15, 2011 Page 10 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000028 0.0000000014 0.0000000011 0.000

lb/mmBtuO2 2.12E-13 1.14E-13 8.97E-14 0.000

ng/dscm 2.89E-04 1.56E-04 1.22E-04 0.000

ng/dscm@7%O2 2.46E-04 1.32E-04 1.04E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000018 0.0000000036 0.0000000014 0.000

lb/mmBtuO2 1.37E-13 2.93E-13 1.14E-13 0.000

ng/dscm 1.86E-04 4.01E-04 1.56E-04 0.000

ng/dscm@7%O2 1.58E-04 3.40E-04 1.33E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000000293 0.000000003 0.00000000118 0.000

lb/mmBtuO2 2.22E-13 2.45E-13 9.62E-14 0.000

ng/dscm 3.03E-04 3.35E-04 1.31E-04 0.000

ng/dscm@7%O2 2.58E-04 2.84E-04 1.11E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000033 0.0000000025 0.0000000019 0.000

lb/mmBtuO2 2.50E-13 2.04E-13 1.55E-13 0.000

ng/dscm 3.41E-04 2.79E-04 2.11E-04 0.000

ng/dscm@7%O2 2.90E-04 2.36E-04 1.79E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000038 0.0000000027 0.0000000011 0.000

lb/mmBtuO2 2.88E-13 2.20E-13 8.97E-14 0.000

ng/dscm 3.92E-04 3.01E-04 1.22E-04 0.000

ng/dscm@7%O2 3.34E-04 2.55E-04 1.04E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000000561 0.0000000072 0.0000000035 0.000

lb/mmBtuO2 4.25E-13 5.87E-13 2.85E-13 0.000

ng/dscm 5.79E-04 8.03E-04 3.89E-04 0.001

ng/dscm@7%O2 4.93E-04 6.81E-04 3.31E-04 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000129 0.000000015 0.0000000122 0.000

lb/mmBtuO2 9.78E-13 1.22E-12 9.94E-13 0.000

ng/dscm 1.33E-03 1.67E-03 1.36E-03 0.001

ng/dscm@7%O2 1.13E-03 1.42E-03 1.16E-03 0.001

Tuesday, February 15, 2011 Page 11 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.000000401 0.000000483 0.000000261 0.000

lb/mmBtuO2 3.04E-11 3.94E-11 2.13E-11 0.000

ng/dscm 4.14E-02 5.39E-02 2.90E-02 0.041

ng/dscm@7%O2 3.53E-02 4.57E-02 2.47E-02 0.035

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.000000017 0.000000026 0.0000000176 0.000

lb/mmBtuO2 1.29E-12 2.12E-12 1.43E-12 0.000

ng/dscm 1.76E-03 2.90E-03 1.96E-03 0.002

ng/dscm@7%O2 1.50E-03 2.46E-03 1.67E-03 0.002

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000463 0.000000033 0.00000002 0.000

lb/mmBtuO2 3.51E-12 2.69E-12 1.63E-12 0.000

ng/dscm 4.78E-03 3.68E-03 2.22E-03 0.004

ng/dscm@7%O2 4.07E-03 3.12E-03 1.89E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000114 0.00000126 0.000000695 0.000

lb/mmBtuO2 8.65E-11 1.03E-10 5.66E-11 0.000

ng/dscm 1.18E-01 1.40E-01 7.73E-02 0.112

ng/dscm@7%O2 1.01E-01 1.19E-01 6.57E-02 0.095

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.000000023 0.0000000219 0.000000014 0.000

lb/mmBtuO2 1.74E-12 1.79E-12 1.14E-12 0.000

ng/dscm 2.37E-03 2.44E-03 1.56E-03 0.002

ng/dscm@7%O2 2.02E-03 2.07E-03 1.33E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000046 0.00000000543 0.0000000033 0.000

lb/mmBtuO2 3.49E-13 4.43E-13 2.69E-13 0.000

ng/dscm 4.75E-04 6.05E-04 3.67E-04 0.000

ng/dscm@7%O2 4.05E-04 5.13E-04 3.12E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000000603 0.0000000017 0.0000000033 0.000

lb/mmBtuO2 4.57E-13 1.39E-13 2.69E-13 0.000

Tuesday, February 15, 2011 Page 12 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

ng/dscm 6.23E-04 1.90E-04 3.67E-04 0.000

ng/dscm@7%O2 5.31E-04 1.61E-04 3.12E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000018 0.0000000026 0.0000000023 0.000

lb/mmBtuO2 1.37E-13 2.12E-13 1.87E-13 0.000

ng/dscm 1.86E-04 2.90E-04 2.56E-04 0.000

ng/dscm@7%O2 1.58E-04 2.46E-04 2.18E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000023 0.0000000015 0.0000000021 0.000

lb/mmBtuO2 1.74E-13 1.22E-13 1.71E-13 0.000

ng/dscm 2.37E-04 1.67E-04 2.33E-04 0.000

ng/dscm@7%O2 2.02E-04 1.42E-04 1.98E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000000069 0.0000000048 0.00000000065 0.000

lb/mmBtuO2 5.23E-14 3.91E-13 5.30E-14 0.000

ng/dscm 7.12E-05 5.35E-04 7.23E-05 0.000

ng/dscm@7%O2 6.06E-05 4.53E-04 6.15E-05 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.000000007 0.0000000046 0.0000000058 0.000

lb/mmBtuO2 5.31E-13 3.75E-13 4.73E-13 0.000

ng/dscm 7.23E-04 5.13E-04 6.45E-04 0.001

ng/dscm@7%O2 6.16E-04 4.35E-04 5.48E-04 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000022 0.000000247 0.000000108 0.000

lb/mmBtuO2 1.67E-11 2.01E-11 8.80E-12 0.000

ng/dscm 2.27E-02 2.75E-02 1.20E-02 0.021

ng/dscm@7%O2 1.93E-02 2.33E-02 1.02E-02 0.018

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000111 0.0000000151 0.00000000777 0.000

lb/mmBtuO2 8.42E-13 1.23E-12 6.33E-13 0.000

ng/dscm 1.15E-03 1.68E-03 8.64E-04 0.001

ng/dscm@7%O2 9.79E-04 1.42E-03 7.35E-04 0.001

Compound: OCDD

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Tuesday, February 15, 2011 Page 13 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Mass_mg 0.000000021 0.000000025 0.000000021 0.000

lb/mmBtuO2 1.59E-12 2.04E-12 1.71E-12 0.000

ng/dscm 2.17E-03 2.79E-03 2.33E-03 0.002

ng/dscm@7%O2 1.85E-03 2.36E-03 1.98E-03 0.002

Compound: OCDF

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.000000018 0.0000000093 0.0000000041 0.000

lb/mmBtuO2 1.37E-12 7.58E-13 3.34E-13 0.000

ng/dscm 1.86E-03 1.04E-03 4.56E-04 0.001

ng/dscm@7%O2 1.58E-03 8.81E-04 3.88E-04 0.001

Compound: Total Dioxins

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.0000000378 0.00000004629 0.0000000334 0.000

lb/mmBtuO2 2.87E-12 3.77E-12 2.72E-12 0.000

ng/dscm 3.90E-03 5.16E-03 3.71E-03 0.004

ng/dscm@7%O2 3.32E-03 4.37E-03 3.15E-03 0.004

Compound: Total Furans

Average

RunNumber PMR1-23-1 PMR1-23-2 PMR1-23-3

Mass_mg 0.00000005234 0.00000003923 0.00000002353 0.000

lb/mmBtuO2 3.97E-12 3.20E-12 1.92E-12 0.000

ng/dscm 5.40E-03 4.37E-03 2.62E-03 0.004

ng/dscm@7%O2 4.60E-03 3.70E-03 2.23E-03 0.004

Location: PMR1 - Gases - Method 10

Compound: Carbon Monoxide

Average

Run 1-CO-1 1-CO-2 1-CO-3

lb/mmBtuO2 3.63E-01 4.28E-01 4.52E-01 0.414

ppm 4.27E+02 5.01E+02 5.32E+02 486.667

ppm@7%O2 3.61E+02 4.26E+02 4.51E+02 412.667

Location: PMR1 - Gases - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1-THC-1 1-THC-2 1-THC-3

lb/mmBtuO2 -6.07E-05 1.35E-03 9.39E-04 0.001

ppm -4.54E-02 1.00E+00 7.01E-01 0.552

ppm@7%O2 -3.84E-02 8.50E-01 5.94E-01 0.469

Location: PMR1 - Gases - Method 6C

Compound: Sulfur Dioxide

Average

Run 1-SO2-1 1-SO2-2 1-SO2-3

lb/mmBtuO2 6.74E-01 6.80E-01 6.74E-01 0.676

ppm 3.47E+02 3.49E+02 3.47E+02 347.667

ppm@7%O2 2.94E+02 2.97E+02 2.94E+02 295.000

Tuesday, February 15, 2011 Page 14 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location: PMR1 - Gases - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1-NOx-1 1-NOx-2 1-NOx-3

lb/mmBtuO2 2.96E-01 2.96E-01 3.01E-01 0.298

ppm 2.12E+02 2.11E+02 2.16E+02 213.000

ppm@7%O2 1.79E+02 1.79E+02 1.83E+02 180.333

Location: PMR1 - Metals - Method 29

Compound: Antimony

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.289 0.278 0.243 0.270

Elb/hr 3.35E-01 3.15E-01 2.72E-01 0.307

lb/mmBtuO2 4.84E-05 4.60E-05 4.22E-05 0.000

mg/dscm 6.62E-02 6.28E-02 5.76E-02 0.062

mg/dscm@7%O2 5.61E-02 5.34E-02 4.90E-02 0.053

Compound: Arsenic

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.0174 0.0159 0.015 0.016

Elb/hr 2.02E-02 1.80E-02 1.68E-02 0.018

lb/mmBtuO2 2.91E-06 2.63E-06 2.61E-06 0.000

mg/dscm 3.99E-03 3.59E-03 3.56E-03 0.004

mg/dscm@7%O2 3.38E-03 3.05E-03 3.03E-03 0.003

Compound: Beryllium

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.0018 0.00178 0.00131 0.002

Elb/hr 2.08E-03 2.02E-03 1.46E-03 0.002

lb/mmBtuO2 3.01E-07 2.95E-07 2.28E-07 0.000

mg/dscm 4.12E-04 4.02E-04 3.11E-04 0.000

mg/dscm@7%O2 3.49E-04 3.42E-04 2.64E-04 0.000

Compound: Cadmium

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.000532 0.000516 0.000366 0.000

Elb/hr 6.16E-04 5.85E-04 4.09E-04 0.001

lb/mmBtuO2 8.91E-08 8.55E-08 6.36E-08 0.000

mg/dscm 1.22E-04 1.17E-04 8.68E-05 0.000

mg/dscm@7%O2 1.03E-04 9.95E-05 7.38E-05 0.000

Compound: Chromium

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.018 0.016 0.014 0.016

Elb/hr 2.08E-02 1.81E-02 1.56E-02 0.018

lb/mmBtuO2 3.01E-06 2.65E-06 2.43E-06 0.000

mg/dscm 4.12E-03 3.61E-03 3.32E-03 0.004

Tuesday, February 15, 2011 Page 15 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

mg/dscm@7%O2 3.49E-03 3.07E-03 2.82E-03 0.003

Compound: Cobalt

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.226 0.212 0.197 0.212

Elb/hr 2.62E-01 2.40E-01 2.20E-01 0.241

lb/mmBtuO2 3.78E-05 3.51E-05 3.43E-05 0.000

mg/dscm 5.18E-02 4.79E-02 4.67E-02 0.049

mg/dscm@7%O2 4.39E-02 4.07E-02 3.97E-02 0.041

Compound: Filterable Particulate

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 188.7 164.7 160.4 171.267

Elb/hr 2.19E+02 1.87E+02 1.79E+02 195.000

lb/mmBtuO2 3.16E-02 2.73E-02 2.79E-02 0.029

mg/dscm 4.32E+01 3.72E+01 3.80E+01 39.467

mg/dscm@7%O2 3.66E+01 3.16E+01 3.23E+01 33.500

Compound: Lead

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.0559 0.0547 0.049 0.053

Elb/hr 6.48E-02 6.20E-02 5.48E-02 0.061

lb/mmBtuO2 9.36E-06 9.06E-06 8.52E-06 0.000

mg/dscm 1.28E-02 1.24E-02 1.16E-02 0.012

mg/dscm@7%O2 1.08E-02 1.05E-02 9.86E-03 0.010

Compound: Manganese

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.286 0.26 0.239 0.262

Elb/hr 3.31E-01 2.95E-01 2.67E-01 0.298

lb/mmBtuO2 4.79E-05 4.31E-05 4.16E-05 0.000

mg/dscm 6.55E-02 5.87E-02 5.67E-02 0.060

mg/dscm@7%O2 5.55E-02 4.99E-02 4.82E-02 0.051

Compound: Nickel

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 2.75 2.45 2.17 2.457

Elb/hr 3.19E+00 2.78E+00 2.42E+00 2.797

lb/mmBtuO2 4.61E-04 4.06E-04 3.77E-04 0.000

mg/dscm 6.30E-01 5.53E-01 5.15E-01 0.566

mg/dscm@7%O2 5.34E-01 4.70E-01 4.38E-01 0.481

Compound: Selenium

Average

RunNumber PMR1-29-1 PMR1-29-2 PMR1-29-3

Mass_mg 0.0399 0.0201 0.0175 0.026

Elb/hr 4.62E-02 2.28E-02 1.96E-02 0.030

lb/mmBtuO2 6.68E-06 3.33E-06 3.04E-06 0.000

mg/dscm 9.14E-03 4.54E-03 4.15E-03 0.006

Tuesday, February 15, 2011 Page 16 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Process Run Data

mg/dscm@7%O2 7.75E-03 3.86E-03 3.53E-03 0.005

Location: PMR1 - PM - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber PMR1-27/28-1 PMR1-27/28-2 PMR1-27/28-3

Mass_mg 41 42.57 44.27 42.613

lb/mmBtuO2 2.63E-02 2.57E-02 2.75E-02 0.027

Compound: Filterable PM2.5

Average

RunNumber PMR1-27/28-1 PMR1-27/28-2 PMR1-27/28-3

Mass_mg 28.3 33.425 31.4 31.042

lb/mmBtuO2 1.82E-02 2.02E-02 1.95E-02 0.019

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber PMR1-27/28-1 PMR1-27/28-2 PMR1-27/28-3

Mass_mg 1.504 0 0.93 0.811

lb/mmBtuO2 9.66E-04 0.00E+00 5.79E-04 0.001

Compound: Organic Condensible Particulate

Average

RunNumber PMR1-27/28-1 PMR1-27/28-2 PMR1-27/28-3

Mass_mg 148.981 1.031 0.806 50.273

lb/mmBtuO2 9.57E-02 6.24E-04 5.01E-04 0.032

Compound: Total Particulate

Average

RunNumber PMR1-27/28-1 PMR1-27/28-2 PMR1-27/28-3

Mass_mg 191.485 43.601 46.006 93.697

lb/mmBtuO2 1.23E-01 2.64E-02 2.86E-02 0.059

Compound: Total PM2.5

Average

RunNumber PMR1-27/28-1 PMR1-27/28-2 PMR1-27/28-3

Mass_mg 178.785 34.456 33.136 82.126

lb/mmBtuO2 1.15E-01 2.08E-02 2.06E-02 0.052

Tuesday, February 15, 2011 Page 17 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil (No. 6) Burned 57898 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/6/2010; 

Start - 10:23; 

End - 12:22

0

10 Residual Oil (No. 6) Burned 58126 gal/hr Method 027/028; 

Run PM-1; Date - 

4/7/2010; Start - 

08:43; End - 13:00

0

11 Residual Oil (No. 6) Burned 57950 gal/hr Method 027/028; 

Run PM-2; Date - 

4/8/2010; Start - 

14:12; End - 17:06

0

12 Residual Oil (No. 6) Burned 58184 gal/hr Method 027/028; 

Run PM-3; Date - 

4/9/2010; Start - 

09:49; End - 12:37

0

2 Residual Oil (No. 6) Burned 57928 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/6/2010; 

Start - 12:23; 

End - 16:36

0

3 Residual Oil (No. 6) Burned 57971 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/6/2010; 

Start - 16:36; 

End - 19:42

0

4 Residual Oil (No. 6) Burned 57921 gal/hr Method 23; Run 

D/F-1; Date - 

4/6/2010; Start - 

09:15; End - 19:23

0

5 Residual Oil (No. 6) Burned 58155 gal/hr Method 23; Run 

D/F-2; Date - 

4/7/2010; Start - 

14:15; End - 23:21

0

6 Residual Oil (No. 6) Burned 57950 gal/hr Method 23; Run 

D/F-3; Date - 

4/8/2010; Start - 

11:48; End - 20:42

0

7 Residual Oil (No. 6) Burned 58097 gal/hr Method 29; Run 

M-1; Date - 

4/7/2010; Start - 

14:32; End - 19:18

0

Tuesday, February 15, 2011 Page 18 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

8 Residual Oil (No. 6) Burned 57994 gal/hr Method 29; Run 

M-2; Date - 

4/8/2010; Start - 

08:32; End - 13:27

0

9 Residual Oil (No. 6) Burned 58009 gal/hr Method 29; Run 

M-3; Date - 

4/8/2010; Start - 

17:31; End - 22:18

0

1 Average Heat Input 7266 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/6/2010; 

Start - 10:23; 

End - 12:22

0

10 Average Heat Input 7295 MMBtu/hr Method 027/028; 

Run PM-1; Date - 

4/7/2010; Start - 

08:43; End - 13:00

0

11 Average Heat Input 7273 MMBtu/hr Method 027/028; 

Run PM-2; Date - 

4/8/2010; Start - 

14:12; End - 17:06

0

12 Average Heat Input 7305 MMBtu/hr Method 027/028; 

Run PM-3; Date - 

4/9/2010; Start - 

09:49; End - 12:37

0

2 Average Heat Input 7269 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/6/2010; 

Start - 12:23; 

End - 16:36

0

3 Average Heat Input 7275 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/6/2010; 

Start - 16:36; 

End - 19:42

0

4 Average Heat Input 7269 MMBtu/hr Method 23; Run 

D/F-1; Date - 

4/6/2010; Start - 

09:15; End - 19:23

0

5 Average Heat Input 7298 MMBtu/hr Method 23; Run 

D/F-2; Date - 

4/7/2010; Start - 

14:15; End - 23:21

0

6 Average Heat Input 7274 MMBtu/hr Method 23; Run 

D/F-3; Date - 

4/8/2010; Start - 

11:48; End - 20:42

0

Tuesday, February 15, 2011 Page 19 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

7 Average Heat Input 7292 MMBtu/hr Method 29; Run 

M-1; Date - 

4/7/2010; Start - 

14:32; End - 19:18

0

8 Average Heat Input 7278 MMBtu/hr Method 29; Run 

M-2; Date - 

4/8/2010; Start - 

08:32; End - 13:27

0

9 Average Heat Input 7281 MMBtu/hr Method 29; Run 

M-3; Date - 

4/8/2010; Start - 

17:31; End - 22:18

0

1 Steam Output 5220 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/6/2010; 

Start - 10:23; 

End - 12:22

0

10 Steam Output 5230 1000 lb Method 027/028; 

Run PM-1; Date - 

4/7/2010; Start - 

08:43; End - 13:00

0

11 Steam Output 5176 1000 lb Method 027/028; 

Run PM-2; Date - 

4/8/2010; Start - 

14:12; End - 17:06

0

12 Steam Output 5172 1000 lb Method 027/028; 

Run PM-3; Date - 

4/9/2010; Start - 

09:49; End - 12:37

0

2 Steam Output 5220 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/6/2010; 

Start - 12:23; 

End - 16:36

0

3 Steam Output 5222 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/6/2010; 

Start - 16:36; 

End - 19:42

0

4 Steam Output 5220 1000 lb Method 23; Run 

D/F-1; Date - 

4/6/2010; Start - 

09:15; End - 19:23

0

5 Steam Output 5232 1000 lb Method 23; Run 

D/F-2; Date - 

4/7/2010; Start - 

14:15; End - 23:21

0

Tuesday, February 15, 2011 Page 20 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

6 Steam Output 5174 1000 lb Method 23; Run 

D/F-3; Date - 

4/8/2010; Start - 

11:48; End - 20:42

0

7 Steam Output 5230 1000 lb Method 29; Run 

M-1; Date - 

4/7/2010; Start - 

14:32; End - 19:18

0

8 Steam Output 5194 1000 lb Method 29; Run 

M-2; Date - 

4/8/2010; Start - 

08:32; End - 13:27

0

9 Steam Output 5170 1000 lb Method 29; Run 

M-3; Date - 

4/8/2010; Start - 

17:31; End - 22:18

0

1 Unit Gross Electrical Output 804 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/6/2010; 

Start - 10:23; 

End - 12:22

0

10 Unit Gross Electrical Output 804 MWg Method 027/028; 

Run PM-1; Date - 

4/7/2010; Start - 

08:43; End - 13:00

0

11 Unit Gross Electrical Output 801 MWg Method 027/028; 

Run PM-2; Date - 

4/8/2010; Start - 

14:12; End - 17:06

0

12 Unit Gross Electrical Output 801 MWg Method 027/028; 

Run PM-3; Date - 

4/9/2010; Start - 

09:49; End - 12:37

0

2 Unit Gross Electrical Output 804 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/6/2010; 

Start - 12:23; 

End - 16:36

0

3 Unit Gross Electrical Output 804 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/6/2010; 

Start - 16:36; 

End - 19:42

0

4 Unit Gross Electrical Output 804 MWg Method 23; Run 

D/F-1; Date - 

4/6/2010; Start - 

09:15; End - 19:23

0

Tuesday, February 15, 2011 Page 21 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

5 Unit Gross Electrical Output 804 MWg Method 23; Run 

D/F-2; Date - 

4/7/2010; Start - 

14:15; End - 23:21

0

6 Unit Gross Electrical Output 801 MWg Method 23; Run 

D/F-3; Date - 

4/8/2010; Start - 

11:48; End - 20:42

0

7 Unit Gross Electrical Output 804 MWg Method 29; Run 

M-1; Date - 

4/7/2010; Start - 

14:32; End - 19:18

0

8 Unit Gross Electrical Output 802 MWg Method 29; Run 

M-2; Date - 

4/8/2010; Start - 

08:32; End - 13:27

0

9 Unit Gross Electrical Output 801 MWg Method 29; Run 

M-3; Date - 

4/8/2010; Start - 

17:31; End - 22:18

0

1 Unit Net Electric Generation 772 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/6/2010; 

Start - 10:23; 

End - 12:22

0

10 Unit Net Electric Generation 773 MWn Method 027/028; 

Run PM-1; Date - 

4/7/2010; Start - 

08:43; End - 13:00

0

11 Unit Net Electric Generation 769 MWn Method 027/028; 

Run PM-2; Date - 

4/8/2010; Start - 

14:12; End - 17:06

0

12 Unit Net Electric Generation 769 MWn Method 027/028; 

Run PM-3; Date - 

4/9/2010; Start - 

09:49; End - 12:37

0

2 Unit Net Electric Generation 772 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/6/2010; 

Start - 12:23; 

End - 16:36

0

3 Unit Net Electric Generation 772 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/6/2010; 

Start - 16:36; 

End - 19:42

0

Tuesday, February 15, 2011 Page 22 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

APCD Run Data

Process Lab Run Data

4 Unit Net Electric Generation 772 MWn Method 23; Run 

D/F-1; Date - 

4/6/2010; Start - 

09:15; End - 19:23

0

5 Unit Net Electric Generation 772 MWn Method 23; Run 

D/F-2; Date - 

4/7/2010; Start - 

14:15; End - 23:21

0

6 Unit Net Electric Generation 769 MWn Method 23; Run 

D/F-3; Date - 

4/8/2010; Start - 

11:48; End - 20:42

0

7 Unit Net Electric Generation 773 MWn Method 29; Run 

M-1; Date - 

4/7/2010; Start - 

14:32; End - 19:18

0

8 Unit Net Electric Generation 770 MWn Method 29; Run 

M-2; Date - 

4/8/2010; Start - 

08:32; End - 13:27

0

9 Unit Net Electric Generation 769 MWn Method 29; Run 

M-3; Date - 

4/8/2010; Start - 

17:31; End - 22:18

0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 179 NOx Emissions 0

2 LOW NOX BURNERS 182 NOx Emissions 0

3 LOW NOX BURNERS 183 NOx Emissions 0

1 CYCLONE SEPARATORS 10.7 Opacity 0

2 CYCLONE SEPARATORS 12.4 Opacity 0

3 CYCLONE SEPARATORS 12.5 Opacity 0

Run Name Value UOM Comments

2 Fuel Chlorine Content 88 mg/kg

2 Fuel Fluorine Content 40 mg/kg

2 Fuel Antimony Content 1.4 mg/kg

2 Fuel Arsenic Content 0.075 mg/kg

2 Fuel Beryllium Content 0.01 mg/kg

2 Fuel Cadmium Content 0.007 mg/kg

2 Fuel Chromium Content 0.079 mg/kg

2 Fuel Cobalt Content 1.1 mg/kg

Tuesday, February 15, 2011 Page 23 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

2 Fuel Lead Content 0.33 mg/kg

2 Fuel Manganese Content 1.4 mg/kg

2 Fuel Nickel Content 12.8 mg/kg

2 Fuel Selenium Content 0.03 mg/kg

2 Fuel Sulfur Content 6350 mg/kg

2 Fuel Proximate Analysis (Carbon) 88.2 %

2 Fuel Proximate Analysis (Hydrogen) 10.33 %

2 Fuel Proximate Analysis (Nitrogen) 0.5 %

2 Fuel Proximate Analysis (Oxygen) 0.5 %

2 Fuel Proximate Analysis (Sulfur) 0.609 %

3 Fuel Higher Heating Value 18500 Btu/lb

3 Fuel Moisture 0.924 %

3 Fuel Mercury Content 0.002 mg/kg

3 Fuel Chlorine Content 75 mg/kg

3 Fuel Fluorine Content 40 mg/kg

3 Fuel Antimony Content 1.3 mg/kg

3 Fuel Arsenic Content 0.083 mg/kg

3 Fuel Beryllium Content 0.008 mg/kg

3 Fuel Cadmium Content 0.007 mg/kg

3 Fuel Chromium Content 0.086 mg/kg

3 Fuel Cobalt Content 1 mg/kg

3 Fuel Lead Content 0.33 mg/kg

3 Fuel Manganese Content 1.3 mg/kg

3 Fuel Nickel Content 12.5 mg/kg

3 Fuel Selenium Content 0.03 mg/kg

3 Fuel Sulfur Content 6150 mg/kg

3 Fuel Proximate Analysis (Carbon) 87.75 %

3 Fuel Proximate Analysis (Hydrogen) 10.4 %

3 Fuel Proximate Analysis (Nitrogen) 0.5 %

3 Fuel Proximate Analysis (Oxygen) 0.5 %

3 Fuel Proximate Analysis (Sulfur) 0.632 %

1 Fuel Higher Heating Value 18500 Btu/lb

1 Fuel Moisture 0.36 %

1 Fuel Mercury Content 0.002 mg/kg

1 Fuel Chlorine Content 79 mg/kg

1 Fuel Fluorine Content 40 mg/kg

1 Fuel Antimony Content 1.3 mg/kg

1 Fuel Arsenic Content 0.079 mg/kg

1 Fuel Beryllium Content 0.009 mg/kg

1 Fuel Cadmium Content 0.006 mg/kg

1 Fuel Chromium Content 0.1 mg/kg

1 Fuel Cobalt Content 1 mg/kg

1 Fuel Lead Content 0.32 mg/kg

Tuesday, February 15, 2011 Page 24 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

1 Fuel Manganese Content 1.4 mg/kg

1 Fuel Nickel Content 13.4 mg/kg

1 Fuel Selenium Content 0.03 mg/kg

1 Fuel Sulfur Content 6530 mg/kg

1 Fuel Proximate Analysis (Carbon) 88.27 %

1 Fuel Proximate Analysis (Hydrogen) 10.52 %

1 Fuel Proximate Analysis (Nitrogen) 0.5 %

1 Fuel Proximate Analysis (Oxygen) 0.5 %

1 Fuel Proximate Analysis (Sulfur) 0.606 %

2 Fuel Higher Heating Value 18500 Btu/lb

2 Fuel Moisture 0.59 %

2 Fuel Mercury Content 0.001 mg/kg

Tuesday, February 15, 2011 Page 25 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Sampling / Stack Data Results Detail

Location PMR1 - D/F - Method 23

Average

Run Number PMR1-23-1 PMR1-23-2 PMR1-23-3

Test Date 4/6/2010 4/7/2010 4/8/2010

Run Start Time 9:15:00 AM 2:15:00 PM 11:48:00 AM

Run Finish Time 5:15:00 PM 10:15:00 PM 7:48:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.987 0.987 0.987 0.987

Barometric Pressure, inches of Mercury 30.18 29.85 29.8 29.943

Average Orifice Meter Differential, inches H2O 1.96 1.63 1.66 1.750

Dry Gas Meter Volume Sampled, cubic feet 351.530 329.990 331.480 337.667

Average Dry Gas Meter Temperature, °F 82.73 83.79 83.69 83.403

Dry Gas Meter Volume Sampled, dscf 342.102 316.770 317.751 325.541

Total Moisture Liquid collected, g 715.9 763 697.9 725.600

Volume of Water Vapor, standard cubic feet 33.70 35.91 32.85 34.153

Moisture Content of Stack Gas, % 8.97 10.18 9.37 9.507

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9103 0.8982 0.9063 0.905

Carbon Dioxide, % 13.03 13.01 13.11 13.050

Oxygen, % 4.58 4.5 4.55 4.543

Carbon Monoxide & Nitrogen, % 82.39 82.49 82.34 82.407

Fuel Factor 1.25 1.26 1.25

Dry Molecular Weight, lb/lb-Mole 30.27 30.26 30.28 30.270

Wet Molecular weight, lb/lb-Mole 29.17 29.01 29.13 29.103

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 30.25 29.92 29.87 30.013

Average Stack Gas Temperature, °F 338.50 342.96 348.75 343.403

Average Velocity Head, inches of H2O 0.7516221288

14947

0.642482887

433608

0.656072276

636916

0.683

Average Stack Gas Velocity, feet/second 59.22 55.36 56.08 56.887

Stack Cross-Sectional Area, square feet 696.685 696.685 696.685 696.685

Dry Volumetric Flow Rate, dry scfm 1,506,480.3 1,366,774.5 1,384,716.8 1,419,323.8

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,475,461.1 2,314,108.9 2,344,205.7 2,377,925.2

33

Percent Isokinetic of Sampling Rate, % 96.7 98.7 97.7 97.700

Percent Excess Air, % 26.7 26.0 26.5 26.400

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 357.4 357.4 357.4

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 26 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 10

Average

Run Number 1-CO-1 1-CO-2 1-CO-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 PM 4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Analyzer Make THERMO THERMO THERMO

Analyzer Model 48i 48i 48i

Analyzer Serial Number INST-CO0017INST-CO0017INST-CO0017

Operating Range 1109 1109 1109 1,109.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 5 5 5 5.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 7.8 10.6 10.71 9.703

Calibration Pre Zero Cylinder Bias 0.66 0.91 0.92 0.830

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID ALM042523-

CO

ALM042523

-CO

ALM042523-

CO

Calibration Pre High Cylinder Instrument Response 553 547.13 544.67 548.267

Calibration Pre High Cylinder Bias 0.09 -0.44 -0.66 -0.337

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 10.6 10.71 10.87 10.727

Calibration Post Zero Cylinder Bias 0.91 0.92 0.93 0.920

Calibration Post Zero Cylinder Drift 0.25 0.01 0.01 0.090

Calibration Post High Cylinder ID ALM042523-

CO

ALM042523

-CO

ALM042523-

CO

Calibration Post High Cylinder Instrument Response 547.13 544.67 542.06 544.620

Calibration Post High Cylinder Bias -0.44 -0.66 -0.9 -0.667

Calibration Post High Cylinder Drift 0.53 0.22 0.24 0.330

Cavg 430.06 499.28 526.63 485.323

Cavg Units ppmvd ppmvd ppmvd

Cgas 427.19 501.1819 531.7489 486.707

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 27 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 25A

Average

Run Number 1-THC-1 1-THC-2 1-THC-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 PM 4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Analyzer Make VIG VIG VIG

Analyzer Model 20 20 20 20.000

Analyzer Serial Number INST-TH0007INST-TH0007INST-TH0007

Operating Range 50 50 50 50.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 6 6 6 6.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.15 0.31 0.32 0.260

Calibration Pre Zero Cylinder Bias 0.26 0.58 0.6 0.480

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID CC115743 CC115743 CC115743

Calibration Pre High Cylinder Instrument Response 14.23 14.1 14.13 14.153

Calibration Pre High Cylinder Bias 0 -0.26 -0.2 -0.153

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.31 0.32 0.36 0.330

Calibration Post Zero Cylinder Bias 0.58 0.6 0.68 0.620

Calibration Post Zero Cylinder Drift 0.32 0.02 8.000000000

00001E-02

0.140

Calibration Post High Cylinder ID CC115743 CC115743 CC115743

Calibration Post High Cylinder Instrument Response 14.1 14.13 14.1 14.110

Calibration Post High Cylinder Bias -0.26 -0.2 -0.26 -0.240

Calibration Post High Cylinder Drift 0.26 0.06 0.06 0.127

Cavg 0.19 1.19 0.95 0.777

Cavg Units ppmvw ppmvw ppmvw

Cgas -0.0454 1.0031 0.7006 0.553

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw -

4.1334768568

3531E-02

0.913043478

26087

0.637676950

998185

0.503

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 28 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 3A CO2

Average

Run Number 1-CO2-1 1-CO2-2 1-CO2-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 PM 4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Analyzer Make THERMO THERMO THERMO

Analyzer Model 410i 410i 410i

Analyzer Serial Number INST-C2-0010 INST-C2-

0010

INST-C2-

0010

Operating Range 19.3 19.3 19.3 19.300

Operating Units % % %

No. Readings/Avg. 240 240 240 240.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.12 -0.04 0.03 0.037

Calibration Pre Zero Cylinder Bias 0.52 -0.31 0.05 0.087

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AAL12025-

CO2

AAL12025-

CO2

AAL12025-

CO2

Calibration Pre High Cylinder Instrument Response 8.72 8.57 8.45 8.580

Calibration Pre High Cylinder Bias 0.31 -0.47 -1.09 -0.417

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response -0.04 0.03 0.11 0.033

Calibration Post Zero Cylinder Bias -0.31 0.05 0.47 0.070

Calibration Post Zero Cylinder Drift 0.83 0.36 0.42 0.537

Calibration Post High Cylinder ID AAL12025-

CO2

AAL12025-

CO2

AAL12025-

CO2

Calibration Post High Cylinder Instrument Response 8.57 8.45 8.7 8.573

Calibration Post High Cylinder Bias -0.47 -1.09 0.21 -0.450

Calibration Post High Cylinder Drift 0.78 0.62 1.3 0.900

Cavg 12.62 12.61 12.71 12.647

Cavg Units %vd %vd %vd

Cgas 12.9967 13.1706 13.2122 13.127

Cgas Units %vd %vd %vd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units %vw %vw %vw

Tuesday, February 15, 2011 Page 29 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 3A O2

Average

Run Number 1-O2-1 1-O2-2 1-O2-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 PM 4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Analyzer Make THERMO THERMO THERMO

Analyzer Model 42i-HL 42i-HL 42i-HL

Analyzer Serial Number INST-N2-0002 INST-N2-

0002

INST-N2-

0002

Operating Range 21.1 21.1 21.1 21.100

Operating Units % % %

No. Readings/Avg. 240 240 240 240.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.08 0.31 0.34 0.243

Calibration Pre Zero Cylinder Bias 0.28 1.37 1.52 1.057

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AAL12025-O2 AAL12025-

O2

AAL12025-

O2

Calibration Pre High Cylinder Instrument Response 12.1 12.23 12.32 12.217

Calibration Pre High Cylinder Bias -0.05 0.57 1 0.507

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.31 0.34 0.39 0.347

Calibration Post Zero Cylinder Bias 1.37 1.52 1.75 1.547

Calibration Post Zero Cylinder Drift 1.09 0.15 0.23 0.490

Calibration Post High Cylinder ID AAL12025-O2 AAL12025-

O2

AAL12025-

O2

Calibration Post High Cylinder Instrument Response 12.23 12.32 12.04 12.197

Calibration Post High Cylinder Bias 0.57 1 -0.33 0.413

Calibration Post High Cylinder Drift 0.62 0.43 1.33 0.793

Cavg 4.61 4.81 4.75 4.723

Cavg Units %vd %vd %vd

Cgas 4.4629 4.5413 4.4908 4.498

Cgas Units %vd %vd %vd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units %vw %vw %vw

Tuesday, February 15, 2011 Page 30 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 6C

Average

Run Number 1-SO2-1 1-SO2-2 1-SO2-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 PM 4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Analyzer Make THERMO THERMO THERMO

Analyzer Model 43i-HL 43i-HL 43i-HL

Analyzer Serial Number INST-S2-0005 INST-S2-

0005

INST-S2-

0005

Operating Range 959 959 959 959.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 1.93 1.58 0.92 1.477

Calibration Pre Zero Cylinder Bias -0.02 -0.06 -0.13 -0.070

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID CC66246 CC66246 CC66246

Calibration Pre High Cylinder Instrument Response 438.1 420.17 426.52 428.263

Calibration Pre High Cylinder Bias -0.15 -2.02 -1.35 -1.173

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 1.58 0.92 0.75 1.083

Calibration Post Zero Cylinder Bias -0.06 -0.13 -0.14 -0.110

Calibration Post Zero Cylinder Drift 0.04 0.07 0.01 0.040

Calibration Post High Cylinder ID CC66246 CC66246 CC66246

Calibration Post High Cylinder Instrument Response 420.17 426.52 425.75 424.147

Calibration Post High Cylinder Bias -2.02 -1.35 -1.43 -1.600

Calibration Post High Cylinder Drift 1.87 0.67 7.999999999

99998E-02

0.873

Cavg 347.86 344.97 345.24 346.023

Cavg Units ppmvd ppmvd ppmvd

Cgas 346.6071 348.5286 346.5914 347.242

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 31 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Gases - Method 7E

Average

Run Number 1-NOx-1 1-NOx-2 1-NOx-3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 10:23:11 AM 12:23:11 PM 4:36:41 PM

Run Finish Time 12:22:41 PM 4:36:11 PM 7:42:41 PM

Carbon Dioxide, % 12.99 13.17 13.21 13.123

Oxygen, % 4.47 4.54 4.49 4.500

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1506474 1506474 1506474 1,506,474.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.98 8.98 8.98 8.980

Analyzer Make THERMO THERMO THERMO

Analyzer Model 42i-HL 42i-HL 42i-HL

Analyzer Serial Number INST-N2-0002 INST-N2-

0002

INST-N2-

0002

Operating Range 1110 1110 1110 1,110.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 1.17 2.33 1.9 1.800

Calibration Pre Zero Cylinder Bias 0.02 0.13 0.09 0.080

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID ALM042523-

NOx

ALM042523

-NOx

ALM042523-

NOx

Calibration Pre High Cylinder Instrument Response 550.55 540.82 533.11 541.493

Calibration Pre High Cylinder Bias -0.09 -0.96 -1.66 -0.903

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 2.33 1.9 1.95 2.060

Calibration Post Zero Cylinder Bias 0.13 0.09 0.09 0.103

Calibration Post Zero Cylinder Drift 0.11 0.04 0 0.050

Calibration Post High Cylinder ID ALM042523-

NOx

ALM042523

-NOx

ALM042523-

NOx

Calibration Post High Cylinder Instrument Response 540.82 533.11 539.82 537.917

Calibration Post High Cylinder Bias -0.96 -1.66 -1.05 -1.223

Calibration Post High Cylinder Drift 0.87 0.7 0.61 0.727

Cavg 212.6 208.64 212.66 211.300

Cavg Units ppmvd ppmvd ppmvd

Cgas 212.0381 211.2166 215.6472 212.967

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 32 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - Metals - Method 29

Average

Run Number PMR1-29-1 PMR1-29-2 PMR1-29-3

Test Date 4/7/2010 4/8/2010 4/8/2010

Run Start Time 2:32:00 PM 8:32:00 AM 5:31:00 PM

Run Finish Time 6:32:00 PM 12:32:00 PM 9:31:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.979 0.979 0.979 0.979

Barometric Pressure, inches of Mercury 29.85 29.74 29.71 29.767

Average Orifice Meter Differential, inches H2O 1.50 1.44 1.29 1.410

Dry Gas Meter Volume Sampled, cubic feet 163.920 163.420 157.840 161.727

Average Dry Gas Meter Temperature, °F 90.31 78.85 85.63 84.930

Dry Gas Meter Volume Sampled, dscf 154.179 156.378 148.957 153.171

Total Moisture Liquid collected, g 372.2 385.7 365.8 374.567

Volume of Water Vapor, standard cubic feet 17.52 18.15 17.22 17.630

Moisture Content of Stack Gas, % 10.20 10.40 10.36 10.320

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.898 0.896 0.8964 0.897

Carbon Dioxide, % 13.01 13.11 13.11 13.077

Oxygen, % 4.5 4.55 4.55 4.533

Carbon Monoxide & Nitrogen, % 82.49 82.34 82.34 82.390

Fuel Factor 1.26 1.25 1.25

Dry Molecular Weight, lb/lb-Mole 30.26 30.28 30.28 30.273

Wet Molecular weight, lb/lb-Mole 29.01 29.00 29.01 29.007

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.92 29.81 29.78 29.837

Average Stack Gas Temperature, °F 346.67 342.79 347.92 345.793

Average Velocity Head, inches of H2O 0.6301237495

63922

0.622965809

240785

0.552692675

012846

0.602

Average Stack Gas Velocity, feet/second 54.95 54.62 51.63 53.733

Stack Cross-Sectional Area, square feet 696.685 696.685 696.685 696.685

Dry Volumetric Flow Rate, dry scfm 1,350,111.9 1,340,540.0 1,258,404.8 1,316,352.2

33

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,296,970.4 2,283,176.1 2,158,190.8 2,246,112.4

33

Percent Isokinetic of Sampling Rate, % 97.2 99.3 100.8 99.100

Percent Excess Air, % 26.0 26.5 26.5 26.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 357.4 357.4 357.4

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 33 of 34
Martin Energy Center, Unit #1, Information Collection Request

6/25/2010

Location PMR1 - PM - OTM - 27/28

Average

Run Number PMR1-27/28-1 PMR1-

27/28-2

PMR1-27/28-

3

Test Date 4/7/2010 4/8/2010 4/9/2010

Run Start Time 8:43:00 AM 2:12:00 PM 9:49:00 AM

Run Finish Time 1:00:00 PM 5:06:00 PM 12:37:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 123 124 125

Nozzle Diameter, inches 0.172 0.172 0.172 0.172

Pitot Tube Coefficient 0.8 0.8 0.8 0.800

Dry Gas Meter Calibration Factor 0.987 0.979 0.979 0.982

Barometric Pressure, inches of Mercury 30.18 29.77 29.71 29.887

Average Orifice Meter Differential, inches H2O 0.40 0.40 0.40 0.400

Dry Gas Meter Volume Sampled, cubic feet 40.720 45.230 43.450 43.133

Average Dry Gas Meter Temperature, °F 73.08 83.79 76.21 77.693

Dry Gas Meter Volume Sampled, dscf 40.193 42.821 41.633 41.549

Total Moisture Liquid collected, g 86.3 91.6 89.7 89.200

Volume of Water Vapor, standard cubic feet 4.06 4.31 4.22 4.197

Moisture Content of Stack Gas, % 9.17 9.14 9.20 9.170

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9083 0.9086 0.908 0.908

Carbon Dioxide, % 13.01 13.11 13.11 13.077

Oxygen, % 4.5 4.55 4.55 4.533

Carbon Monoxide & Nitrogen, % 82.49 82.34 82.34 82.390

Fuel Factor 1.26 1.25 1.25

Dry Molecular Weight, lb/lb-Mole 30.26 30.28 30.28 30.273

Wet Molecular weight, lb/lb-Mole 29.14 29.16 29.15 29.150

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 30.25 29.84 29.78 29.957

Average Stack Gas Temperature, °F 338.25 350.67 346.17 345.030

Average Velocity Head, inches of H2O 0.7380687531

01795

0.701890213

841434

0.721110942

307571

0.720

Average Stack Gas Velocity, feet/second 55.91 55.31 55.97 55.730

Stack Cross-Sectional Area, square feet 696.685 696.685 696.685 696.685

Dry Volumetric Flow Rate, dry scfm 1,419,597.7 1,364,555.3 1,384,838.9 1,389,663.9

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,337,099.5 2,312,018.8 2,339,607.6 2,329,575.3

00

Percent Isokinetic of Sampling Rate, % 99.4 109.3 103.8 104.167

Percent Excess Air, % 26.0 26.5 26.5 26.333

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 357.4 357.4 357.4

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 34 of 34