### (918) 307-8865 or (888) 461-8778 www.airhygiene.com Corporate Headquarters 5634 S. 122nd E. Ave. Ste. F Tulsa, Oklahoma 74146 Las Vegas Office 5925 E. Lake Mead Blvd. Las Vegas, Nevada 89156 Philadelphia Office 8900 State Road Philadelphia, Pennsylvania 19136 Houston Office 1920 Treble Drive Humble, Texas 77338 

# S T A C K E M I S S I O N S S T U D Y F O R T H E C A T E R P I L L A R G 3 5 2 0 C , U N I T S 1

- 6 P R E P A R E D F O R E N E R G Y D E V E L O P M E N T , I N C

. A T T H E C O V E L G A R D E N S L A N D F I L L G A S P O W E R S T A T I O N R E G U L A T E D E N T I T Y # : R N 1 0 4 1 5 6 0 6 2 C U S T O M E R R E F E R E N C E # : C N 6 0 1 5 2 7 5 3 4 S A N A N T O N I O , T E X A S A U G U S T 2 7 , 2 0 0 9

# STACK EMISSIONS STUDY FOR THE CATERPILLAR G3520C, UNITS 1-6 PREPARED FOR ENERGY DEVELOPMENT, INC. AT THE COVEL GARDENS LANDFILL GAS POWER STATION REGULATED ENTITY #: RN104156062 CUSTOMER REFERENCE #: CN601527534 SAN ANTONIO, TEXAS AUGUST 27, 2009

Prepared and Reviewed by:

Pat McGovern, QSTI, Project Mana ger Nathan Arthur, Test Manager

Thomas K. Graham, PE, QSTI, Director of Operations

## i 

## Table of Contents
1.0 INTRODUCTION __________________________________________________________________ 1 1.1 TEST PURPOSE AND OBJECTIVES ______________________________________________________ 1 1.2 SUMMARY OF TEST PROGRAM _________________________________________________________ 1 1.2.1 Participating Organizations ________________________________________________________________________ 1 1.2.2 Industry _______________________________________________________________________________________ 1 1.2.3 Plant Location __________________________________________________________________________________ 1 1.2.4 Equipment Te sted _______________________________________________________________________________ 1 1.2.5 Emission Points _________________________________________________________________________________ 1 1.2.6 Pollutants Measured _____________________________________________________________________________ 1 1.2.7 Date of Emissi on Test ____________________________________________________________________________ 1 

## 1.3 KEY PERSONNEL ______________________________________________________________________ 2 

## 2.0 SUMMARY OF TEST RESULTS ____________________________________________________ 2 3.0 SOURCE OPERATION _____________________________________________________________ 9 3.1 PROCESS DESCRIPTION _______________________________________________________________ 9 3.2 SAMPLING LOCATION __________________________________________________________________ 9 

## 4.0 SAMPLING AND ANALYTICAL PROCEDURES ______________________________________ 9 4.1 TEST METHODS ________________________________________________________________________ 9 4.2 INSTRUMENT CONFIGURATION AND OPERATIONS FOR GAS ANALYSIS __________________ 9 

## APPENDICES Appendix A Test Results and Calculations Appendix B Unit Operation Parameters Appendix C Calibration Gas Certifications Appendix D Quality Assurance and Quality Control Data Appendix E Fuel Analysis Records

## ed-09-sanantonio.tx-ecom#3-rpt 1 

## Stack Emissions Study Caterpillar G3520C, Units 1-6

Energy Development, Inc. Covel Gardens Landfill Gas Power Station San Antonio, Texas

August 27, 2009

1.0 INTRODUCTION Air Hygiene International, Inc. (A ir Hygiene) has completed the stack sampling survey for nitrogen oxides (NOx), carbon monoxide (CO), and oxygen (O 2 

## ) from the exhaust of the Ca terpillar G3520C, Units 1-6 for Energy Development, Inc. at the Covel Gardens Landfill G as Power Station near San Antonio, Texas. This report details the background, results, process description, and the sampling/analysis methodology of the stack sampling survey conducted on August 27, 2009. 

## 1.1 TEST PURPOSE AND OBJECTIVES The purpose of the test was to conduct the quarterly emi ssion test to document levels of selected pollutants at normal operation levels of the designate d engines. The information will be used to confirm compliance with the air quality permit requirements. The specific objective w as to determine the emission concentration of NOx, CO, and O 2 

## from the exhaust of Energy Developmen t, Inc.’s Caterpillar G3520C, Units 1-6. 

## 1.2 SUMMARY OF TEST PROGRAM The following list details pertinent inform ation related to this specific project: 1.2.1 Participating Organizations
• Energy Development, Inc.
• Air Hygiene 1.2.2 Industry
• Electric Utility 1.2.3 Plant Location
• Covel Gardens Landfill Gas Power Station near San Antonio, Texas 1.2.4 Equipment Tested
• Caterpillar G3520C, Units 1-6, Emission Point Numbers: E1 – E6 1.2.5 Emission Points
• Exhaust from the Caterpillar G3520C, Units 1-6 1.2.6 Pollutants Measured
• NOx
• CO
• O 2 

## 1.2.7 Date of Emission Test
• August 27, 2009

## ed-09-sanantonio.tx-ecom#3-rpt 2 

## 1.3 KEY PERSONNEL Energy Development, Inc.: Liza Mireles 713-300-3323 Energy Development, Inc.: Jimmy Romine 713-781-5353 Air Hygiene: Nathan Arthur 918-307-8865


## 2.0 SUMMARY OF TEST RESULTS Results from the sampling conducted on Energy Developmen t, Inc.’s Caterpillar G3520C, Units 1-6 located at the Covel Gardens Landfill Gas Power Station on August 27, 2009 are summarized in the following tables.

## Date: Location: 

# Stack Gas Flow Rate: Method 2

Test # Brake Horsepower O 2 

### Conc. (%) Fuel Heating Value (Btu/SCF) [HHV] F Factor-Dry Oxy. (DSCFex/MMBtu) 

### Stack Flow (SCF/hr) 1 2,211 8.40 475 9,444 250,000 2 2,211 8.40 475 9,444 250,000 3 2,211 8.40 475 9,444 250,000 Average 2,211 8.40 475 9,444 250,000 

# NOx Mass Emission Rate

Test # Brake Horsepower NOx Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 56.25 46.01 0.34 1.68 7.36 

# EMISSION CALCULATIONS SUMMARY TABLES Energy Developments August 27, 2009 

# TABLE 2.1 UNIT 1 EMISSIONS REPORT

Caterpillar G3520-C; E-1 San Antonio, Texas Unit: Client:

2 2,211 56.00 46.01 0.34 1.67 7.32 3 2,211 55.50 46.01 0.34 1.66 7.26 Average 2,211 55.92 46.01 0.34 1.67 7.31 0.60 

# CO Mass Emission Rate

Test # Brake Horsepower CO Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 584.00 28.00 2.18 10.61 46.48 2 2,211 582.13 28.00 2.17 10.58 46.33 3 2,211 583.00 28.00 2.17 10.59 46.40 Average 2,211 583.04 28.00 2.17 10.59 46.40 2.80
Weather Data 29.94 in. Hg 55 % 73 o F 

### Unit Data 27.90 1200 rpm 1450 kW 644 o F 2211 hp Barometric Pressure Relative Humidity Ambient Temperature

Brake Horsepower Air Fuel Ratio Engine Speed in RPM Load in KW Exhaust Temperature 

### Permit Limit

Permit Limit

ed-09-sanantonio .tx-ecom# 3 -gases 3

## Date: Location: 

# Stack Gas Flow Rate: Method 2

Test # Brake Horsepower O 2 

### Conc. (%) Fuel Heating Value (Btu/SCF) [HHV] F Factor-Dry Oxy. (DSCFex/MMBtu) 

### Stack Flow (SCF/hr) 1 2,211 8.36 475 9,444 250,000 2 2,211 8.35 475 9,444 250,000 3 2,211 8.33 475 9,444 250,000 Average 2,211 8.35 475 9,444 250,000 

# NOx Mass Emission Rate

Test # Brake Horsepower NOx Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 55.00 46.01 0.34 1.64 7.19 

# TABLE 2.2 UNIT 2 EMISSIONS REPORT

EMISSION CALCULATIONS SUMMARY TABLES Energy Developments August 27, 2009 Client: Caterpillar G3520-C; E-2 San Antonio, Texas

Unit:

2 2,211 52.50 46.01 0.32 1.57 6.87 3 2,211 54.50 46.01 0.33 1.63 7.13 Average 2,211 54.00 46.01 0.33 1.61 7.06 0.60 

# CO Mass Emission Rate

Test # Brake Horsepower CO Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 628.50 28.00 2.34 11.42 50.02 2 2,211 621.75 28.00 2.32 11.30 49.48 3 2,211 618.25 28.00 2.30 11.23 49.21 Average 2,211 622.83 28.00 2.32 11.32 49.57 2.80
Weather Data 29.94 in. Hg 73 % 75 o F 

### Unit Data 26.50 1200 rpm 1502 kW 640 o F 2211 hp Barometric Pressure Relative Humidity Ambient Temperature

Air Fuel Ratio 

### Permit Limit

Permit Limit

Engine Speed in RPM Load in KW Exhaust Temperature Brake Horsepower



### ed-09-sanantonio .tx-ecom# 3 -gases 4

## Date: Location: 

# Stack Gas Flow Rate: Method 2

Test # Brake Horsepower O 2 

### Conc. (%) Fuel Heating Value (Btu/SCF) [HHV] F Factor-Dry Oxy. (DSCFex/MMBtu) 

### Stack Flow (SCF/hr) 1 2,211 8.48 475 9,444 250,000 2 2,211 8.50 475 9,444 250,000 3 2,211 8.50 475 9,444 250,000 Average 2,211 8.49 475 9,444 250,000 

# NOx Mass Emission Rate

Test # Brake Horsepower NOx Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 49.75 46.01 0.30 1.49 6.51 

# UNIT 3 EMISSIONS REPORT

EMISSION CALCULATIONS SUMMARY TABLES Energy Developments August 27, 2009 Client: 

# TABLE 2.3

Caterpillar G3520-C; E-3 San Antonio, Texas Unit:

2 2,211 48.63 46.01 0.30 1.45 6.36 3 2,211 49.38 46.01 0.30 1.47 6.46 Average 2,211 49.25 46.01 0.30 1.47 6.44 0.60 

# CO Mass Emission Rate

Test # Brake Horsepower CO Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 513.38 28.00 1.91 9.33 40.86 2 2,211 510.50 28.00 1.90 9.28 40.63 3 2,211 511.13 28.00 1.91 9.29 40.68 Average 2,211 511.67 28.00 1.91 9.30 40.72 2.80
Weather Data 29.96 in. Hg 77 % 71 o F 

### Unit Data 26.20 1200 rpm 1600 kW 645 o F 2211 hp Barometric Pressure Relative Humidity Ambient Temperature

Air Fuel Ratio 

### Permit Limit

Permit Limit

Engine Speed in RPM Load in KW Exhaust Temperature Brake Horsepower



### ed-09-sanantonio .tx-ecom# 3 -gases 5

## Date: Location: 

# Stack Gas Flow Rate: Method 2

Test # Brake Horsepower O 2 

### Conc. (%) Fuel Heating Value (Btu/SCF) [HHV] F Factor-Dry Oxy. (DSCFex/MMBtu) 

### Stack Flow (SCF/hr) 1 2,211 8.50 475 9,444 250,000 2 2,211 8.50 475 9,444 250,000 3 2,211 8.50 475 9,444 250,000 Average 2,211 8.50 475 9,444 250,000 

# NOx Mass Emission Rate

Test # Brake Horsepower NOx Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 49.75 46.01 0.30 1.49 6.51 

# UNIT 4 EMISSIONS REPORT

EMISSION CALCULATIONS SUMMARY TABLES Energy Developments August 27, 2009 Client: 

# TABLE 2.4

Caterpillar G3520-C; E-4 San Antonio, Texas Unit:

2 2,211 48.38 46.01 0.30 1.44 6.33 3 2,211 47.25 46.01 0.29 1.41 6.18 Average 2,211 48.46 46.01 0.30 1.45 6.34 0.60 

# CO Mass Emission Rate

Test # Brake Horsepower CO Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 551.88 28.00 2.06 10.03 43.92 2 2,211 552.50 28.00 2.06 10.04 43.97 3 2,211 548.13 28.00 2.04 9.96 43.62 Average 2,211 550.83 28.00 2.05 10.01 43.84 2.80
Weather Data 29.96 in. Hg 55 % 82 o F 

### Unit Data 27.30 1200 rpm 1600 kW 635 o F 2211 hp Barometric Pressure Relative Humidity Ambient Temperature

Air Fuel Ratio 

### Permit Limit

Permit Limit

Engine Speed in RPM Load in KW Exhaust Temperature Brake Horsepower



### ed-09-sanantonio .tx-ecom# 3 -gases 6

## Date: Location: 

# Stack Gas Flow Rate: Method 2

Test # Brake Horsepower O 2 

### Conc. (%) Fuel Heating Value (Btu/SCF) [HHV] F Factor-Dry Oxy. (DSCFex/MMBtu) 

### Stack Flow (SCF/hr) 1 2,211 8.29 475 9,444 250,000 2 2,211 8.24 475 9,444 250,000 3 2,211 8.30 475 9,444 250,000 Average 2,211 8.28 475 9,444 250,000 

# NOx Mass Emission Rate

Test # Brake Horsepower NOx Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 61.75 46.01 0.38 1.84 8.08 

## Client:

Unit: 

# UNIT 5 EMISSIONS REPORT

EMISSION CALCULATIONS SUMMARY TABLES Energy Developments August 27, 2009 

# TABLE 2.5

Caterpillar G3520-C; E-5 San Antonio, Texas

2 2,211 62.63 46.01 0.38 1.87 8.19 3 2,211 61.00 46.01 0.37 1.82 7.98 Average 2,211 61.79 46.01 0.38 1.85 8.08 0.60 

# CO Mass Emission Rate

Test # Brake Horsepower CO Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 572.13 28.00 2.13 10.40 45.53 2 2,211 567.38 28.00 2.12 10.31 45.16 3 2,211 559.00 28.00 2.08 10.16 44.49 Average 2,211 566.17 28.00 2.11 10.29 45.06 2.80
Weather Data 29.98 in. Hg 43 % 85 o F 

### Unit Data 27.70 1200 rpm 1600 kW 643 o F 2211 hp Engine Speed in RPM Barometric Pressure Relative Humidity

Load in KW Exhaust Temperature Brake Horsepower 

### Permit Limit

Permit Limit

Ambient Temperature

Air Fuel Ratio



### ed-09-sanantonio .tx-ecom# 3 -gases 7

## Date: Location: 

# Stack Gas Flow Rate: Method 2

Test # Brake Horsepower O 2 

### Conc. (%) Fuel Heating Value (Btu/SCF) [HHV] F Factor-Dry Oxy. (DSCFex/MMBtu) 

### Stack Flow (SCF/hr) 1 2,211 8.61 475 9,444 250,000 2 2,211 8.60 475 9,444 250,000 3 2,211 8.63 475 9,444 250,000 Average 2,211 8.61 475 9,444 250,000 

# NOx Mass Emission Rate

Test # Brake Horsepower NOx Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 49.00 46.01 0.30 1.46 6.41 

## Client:

Unit: 

# TABLE 2.6

Caterpillar G3520-C; E-6 San Antonio, Texas



# UNIT 6 EMISSIONS REPORT

EMISSION CALCULATIONS SUMMARY TABLES Energy Developments August 27, 2009

2 2,211 49.63 46.01 0.30 1.48 6.49 3 2,211 48.00 46.01 0.29 1.43 6.28 Average 2,211 48.88 46.01 0.30 1.46 6.39 0.60 

# CO Mass Emission Rate

Test # Brake Horsepower CO Conc. (ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr) 1 2,211 495.75 28.00 1.85 9.01 39.46 2 2,211 497.88 28.00 1.86 9.05 39.63 3 2,211 490.88 28.00 1.83 8.92 39.07 Average 2,211 494.83 28.00 1.84 8.99 39.38 2.80
Weather Data 30.00 in. Hg 37 % 89 o F 

### Unit Data 27.40 1200 rpm 1500 kW 645 o F 2211 hp Brake Horsepower 

### Permit Limit

Permit Limit

Engine Speed in RPM Load in KW Exhaust Temperature Barometric Pressure Relative Humidity Ambient Temperature

Air Fuel Ratio



### ed-09-sanantonio .tx-ecom# 3 -gases 8

## ed-09-sanantonio.tx-ecom#3-rpt 9 

## 3.0 SOURCE OPERATION 3.1 PROCESS DESCRIPTION The units tested were Caterpillar G3520C, Units 1-6. The engines are rated at 2,172 horsepower. The engine emissions are vented to the atmosphere through an exha ust system extending from the engine. The sample ports were located on a horizontal run connecting to the exhaus t stack. All exhaust samples were continuously drawn from the exhaust stack at the sample ports. 

## 3.2 SAMPLING LOCATION The sample ports were located approximately nine feet above grade level on the exhaust system in a horizontal run connected to the exhaust stack. The horizontal runs measure approximate ly 18 inches in diameter. The ports are at least 2.0 duct diameters downstream from the last point of interference and 0.5 duct diameters upstream from the next point of interference. All exhaust sampl es for gaseous emissions were continuously drawn from the exhaust system at the sample ports from a singl e point near the center of each horizontal run.


## 4.0 SAMPLING AND AN ALYTICAL PROCEDURES 4.1 TEST METHODS The emission tests on the Caterpillar G3520C, Units 1-6 at the Covel Gardens Landfill Gas Power Station were performed following the United States Environmental Prot ection Agency (EPA) methods described by the Code of Federal Regulations (CFR). Table 4.1 outlines the specific methods performed on August 27, 2009. TABLE 4.1 SUMMARY OF SAMPLING METHODS

Pollutant or Parameter Sampling Method Analysis Method Stack Flow Rate EPA Method 2 S-Type Pitot Tube O 2 

### , NOx, CO EPA CTM-034 Electrochemical Cell



## 4.2 INSTRUMENT CONFIGURATION AND OPERATIONS FOR GAS ANALYSIS The sampling and analysis procedures used during these t ests conform with the methods outlined in the Code of Federal Regulations (CFR), Title 40, Part 60, Appendix A, Method 2; and 40 CFR 63, Appendix A, Conditional Test Method (CTM)-034. Figure 4.1 depicts the sample system used for the NOx, CO, and O 2 

## tests. A stainless steel probe was inserted into the sample ports of the stack to extract gas measu rements from the emission stream. The gas sample was continuously pulled through the prob e and transported, via heat-traced Teflon® tubing, to a stainless steel minimum-contact condenser designed to dry the sample. Transportation of the sample, through Teflon® tubing, continued into the sample manifold within the portable analyzer via a stainless steel/Teflon® diaphragm pump. From the manifold, the sample was partitioned to the NOx, CO, and O 2 

## cells.

## ed-09-sanantonio.tx-ecom#3-rpt 10 Gaseous calibration standards were pr ovided in aluminum cylinders with the concentrations certified by the vendor. EPA Protocol No. 1 was used to determine th e cylinder concentrations where applicable (i.e. NOx calibration gases). Table 4.2 provides a description of the analyzer used for the instrument portion of the tests. All data from the continuous monitoring instrument w as recorded using the Advanced DAS EC OM Software. Data records can be found in Appendix A and B of this report. Three test runs of approximately 10 minutes each were conducted on the Ca terpillar G3520C, Units 1-6 in the "as found" operating condition for NOx, CO, and O 2 

## . Exhaust flow rates were measured on Unit 2 at hi gh load during the May 9, 2006 initial compliance demonstration. The Unit 2 exhaust flow rate determin ed in accordance with EPA Method 2 is representative of all units and is used to calculate emission rates. The stack gas analysis for O 2 

## , NOx, and CO concentration was performed in accordance with the procedures set forth in EPA CTM-034. The analyzer uses an electrochemical cell. TABLE 4.2 ANALYTICAL INSTRUMENTATION

Parameter Model & Manufacturer Max. Ranges Sensitivity Detection Principle

O 2 

### , NOx, and CO ECOM - AC 21%, 4000 ppm, 40,000

ppm 0.1 ppm Electrochemical cellFigure 4.1PORTABLE ANALYZERE:\SHARED\DRAWINGS\ECOM SCHEMATIC.PPT 04/04/06 DRAWING:06-001 TKG COPYRIGHT©2006 AIR HYGIENE INTERNATIONAL, INC.5634 S. 122ndEast Ave, Suite FTulsa, Oklahoma 74146www.airhygiene.com(888) 461-8778

STACK flowsampleconfiguration SAMPLE LINEGASCONDITIONERCALIBRATION/DRIFTGAS BOTTLES calibration/ drift lineO2ANALYZERCOANALYZERNOxANALYZERTHCANALYZERSO2ANALYZER (optional)HYPERLOGGERDATARECORDERcalibrationconfigurationPROBEPROBE ELECTROCHEMICAL CELL

# APPENDIX A TEST RESULTS AND CALCULATIONSEXAMPLE CALCULATIONS (FFACTOR) Mark's Std Hdbk, 10th ed.,pg 4-26 High Heat Value Dry (HHV dry ), calc for Methane (single component for the fuel gas)

%

Mark's Std Hdbk, 10th ed., pg 4-26 Low Heat Value Dry (LHV dry ), calc for Methane (single component for the fuel gas)

%

Civil Eng. Ref. Man.,7th Ed.,pg 14-9/GPA Ref. Bulletin 181-86, App. C High Heat Value Wet (HHV wet ), calc for entire sample (all components of the fuel gas)
Btu/SCF

Civil Eng. Ref. Man.,7th Ed.,pg 14-9/GPA Ref. Bulletin 181-86, App. C Low Heat Value Wet (LHV wet ), calc for entire sample (all components of the fuel gas)
Btu/SCF

Lbs Component per Lb-Mol of Gas (CM), calc for Methane (single component for the fuel gas)
% l b

ASTM D 3588 Btu per Lb of Gas Gross ( GCV ) Fuel Molecular Weight (MW Fuel ) MW Fuel = lb/lb-mol + lb/lb-mol x + etc. = RM 19, (07-19-06), 12.2 Emission Rates of PM, SO2, and NOx. Select from the following sections the applicable procedure to compute the PM, SO2, or NOx emission rate (E) in lb/MMBtu. The pollutant concentration must be in lb/scf and the F factor must be in scf/MMBtu. If the pollutant concentration (C) is not in the appropriate units, use Table 19–1 in Section 17.0 to make the proper conversion. An F factor is the ratio of the gas volume of the products of combustion to the heat content of the fuel. The dry F factor (Fd) includes all components of combustion less water, the wet F factor (Fw) includes all components of combustion, and the carbon F factor (Fc) includes only carbon dioxide.

ft 3 /lbmol 385.23 lb/lb-mol

= 6,472.00 Btu/lb = 7.65 Btu/SCF 1.0236 = Btu SCF 427.27

Btu/SCF 463.60 =

417.42

=

LHV dry = 47.70 x 895.75 100.00 Btu
= SCF 474.54 Btu SCF HHV dry = 47.70 x 994.85 100.00 SCF Btu

16.04 427.27

x CM = 47.70 100.00

lb/lb-mol 0.00 28.246 474.54 1.0236

GCV = 474.54 lb-mol

Btu/SCF

28.246 LHV wet =

lb/lb-mol HHV wet = RM 19, (07-19-06), 2.0 Summary of Method, 2.1 Emission Rates. Oxygen (O2) or carbon dioxide (CO2) concentrations and appropriate F factors (ratios of combustion gas volumes to heat inputs) are used to calculate pollutant emission rates from pollutant concentrations.

7.65 

### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

= GCM M SCF Btu HHV dry 100 / %



### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

= NCM M SCF Btu LHV dry 100 / %



### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

=− MW M mol lb lb CM 100 / %



## ( ) () 

# [ ] ∑ =⋅ CM mol lblb MW Fuel / 

### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ ×
= Fuel dry MW G HHV lb Btu GCV /

⎤ ⎡ × G

LHV ⎤ ⎡ l

MW factor DW

HHV SCF Btu HHV dry wet ./

)/( =

factor DW

LHV SCF Btu LHV dry wet ./

)/( =

lb/lb-mol Btu per Lb of Gas Net ( NCV )

= x Weight Percent of Component (C % ), methane RM 19, (07-19-06), Weight Percent of Volatile Organic Compounds (VOC % )
lb/lb-mol lb/lb-mol VOC % = % + % + % + etc. = %

RM 19, (07-19-6), 12.1 Nomenclature
H C S N 2 O 2
Note: Lack of significant figures may cause rounding errors between actual calculations and example calculations. K (scf/lb)/%
1.53

0.46 3.64

0.14 0.57 F d = x 10 6 Btu 385.23 ft 3 /lbmol

RM 19, (07-19-06), 12.3.2 Determined F Factors . If the fuel burned is not listed in Table 19–2 or if the owner or operator chooses to determine an F factor rather than use the values in Table 19–2, use the procedure below: 12.3.2.1 Equations. Use the eq

+ 28.25

3.64 SCF 0.00

lb
= x x 35.97

0.46 SCF 12.69 % 9,444.22 SCF 6,472.00 Btu MMBtu MMBtu lb . %

lb . % lb . %

lb . % x 6.81 %

0.14 SCF x 0.00

0.00 % x lb . % SG =

0.00 0.9753

27.09 % 28.25 7.65 x 100 C % = = 5,827.37 Btu/lb 28.246 lb/lb-mol NCV = 427.27 Btu/SCF

=

% +

- Eq. 19-13

1.53 SCF

44.52 % x + 0.57 SCF 0.00 28.96 lb/lb-mol ASTM D 3588 (SG) Specific Gravity 

### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

= GCM M SCF Btu HHV dry 100 / %



### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

= NCM M SCF Btu LHV dry 100 / %



### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

=− MW M mol lb lb CM 100 / %



## ( ) () 

# [ ] ∑ =⋅ CM mol lblb MW Fuel / 

### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ ×
= Fuel dry MW G HHV lb Btu GCV /



### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡ ×
= Fuel dry MW GLHV lb Btu NCV /



### ( ) ⎥ ⎥ ⎦ ⎤ ⎢ ⎢ ⎣ ⎡ × ⎟ ⎟ ⎠ ⎞ ⎜ ⎜ ⎝ ⎛

= 100 % % Fuel MW

CM C ⎥ ⎦ ⎤ ⎢ ⎣ ⎡

= AIR Fuel MW MW SG



### ( ) ⎥ ⎦ ⎤ ⎢ ⎣ ⎡

= 

## ∑ 18 8

83 % % % HC

HC M VOC factor DW

HHV SCF Btu HHV dry wet ./

)/( =

factor DW

LHV SCF Btu LHV dry wet ./

)/( =



### ( ) GCV OKNKSKCKHKK F o n s c hd d %%%%% −+++ =

ed-09-sanantonio.tx-ecom# 3 -gases App. AEXAMPLE CALCULATIONS (RUNS) Emissions Rate (lb/hr)

ppm lb

Emissions Rate (ton/year)

lb hr ton

Emissions Rate (g/hp-hr) Calculation for grams per horsepower-hour. Calculate, as follows: (calc for NOx gas Run 1, if applicable)

lb g hp
Note: Lack of significant figures may cause rounding errors between actual calculations and example calculations. SCFH x x 46.01 385.23 Calculation for pound per hour emission rate. Calculate, as follows: (calc for NOx gas Run 1, if applicable)
250,000

7.36 year E lb/hr = 56.25 1.68

8,760
= lb/lb-mol hr

year Calculation for tons per year emission rate based on 8760 hours per year. Calculate, as follows: (calc for NOx gas Run 1, if ap plicable) = SCF/lb-mol 10 6 ppm/part

x 2000 lb

hp*hr 1 0

. 3 4
= x

x ton

E g/hp-hr = 1.68 hr

2,211 hr 1.68 x 453.6 g lb E ton/yr = G MW QC E S Gas hr lb × ×= 6 / 10

2000 / / year hr lb yr ton hr E E ×
=

hp E or mw E E hr lb hr lb hrhp g 6. 453 022

. 1314 6.

453 / / / × × × =

⋅

ed-09-sanantonio.tx-ecom# 3 -gases App. A

## ed-09-sanantonio.tx-ecom#3-rpt 

## EMISSION CALCULATIONS Mass Emission Rate Calculations


## G

MW Q CRA hr lb E S 

## × × = 6 

## 10 ) / ( CRA = corrected raw average Qs = stack gas flow rate (Method 19) MW = molecular weight (lb/lb-mol) G = ideal gas conversion factor


## bhp E hr hp g E hr lb 

## 6

. 453 ) / ( / 

## × = ⋅ bhp = brake horsepower



## 2000 ) / ( / year hr lb 

## hr E yr ton E ×
= hr year 

## = hours per year

# TEST RESULTS AND CALCULATIONS Unit 1 Emissions DataLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:00:15 (%) (ppm) (ppm) (ppm) 11.2 380.5 6.5 37.5 89.1 2.5 8.4 595.3 8.0 50.0 89.8 2.5 8.4 585.0 8.0 48.0 89.8 2.5 8.4 589.0 8.0 48.5 90.2 2.5 8.4 589.3 8.0 49.3 89.9 2.5 8.4 587.0 8.0 49.0 8.4 587.0 8.0 49.0 8.4 585.0 8.0 47.0 8.4 584.0 8.0 49.0 89.2 2.5 8.4 584.0 8.0 49.0 8.4 583.0 8.0 48.0 8.4 581.0 8.0 47.0 8.4 581.0 8.0 48.0 88.9 2.5 8.4 584.0 8.0 48.3

8.4 582.3 8.0 48.0 88.9 2.5 20.5 153.8 3.8 7.3 88.4 2.5 21.0 7.8 3.0 3.0 88.6 2.5 21.0 4.5 2.8 2.3 89.3 2.5

Stop Time:

Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Emission Point: 1 Run #:

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314

Date: 8/27/2009

t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Source Test

RAMPUP PHASE Cell Temp Flow Rate

t 8

t 10 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:15

0:10:00 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 t 13

## REFRESH PHASE t 9

t 14 t 15 t 7 1

9121OCVNXH San Antonio, Texas

t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes Sample Flow Rate are within specifications (±10% or as verified)

ed-09-sanantonio.tx-ecom# 3 -gases Unit 1Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:10:15 (%) (ppm) (ppm) (ppm) 9.2 444.0 6.8 42.5 88.9 2.5 8.5 590.8 8.0 46.0 89.1 2.5 8.4 587.0 8.0 46.5 89.9 2.5 8.4 581.5 8.0 47.0 89.7 2.5 8.4 589.0 8.0 48.3 89.7 2.5 8.4 583.0 8.0 47.0 8.4 578.0 8.0 46.0 8.4 576.0 8.0 47.0 8.4 577.0 8.0 47.0 89.9 2.5 8.4 582.0 8.0 48.0 8.4 585.0 8.0 49.0 8.4 587.0 8.0 50.0 8.4 589.0 8.0 50.0 89.3 2.5 8.4 582.1 8.0 48.0

8.4 585.8 8.0 49.3 89.3 2.5 20.2 179.0 4.0 9.0 89.3 2.5 21.0 7.8 3.0 3.0 89.1 2.5 21.0 4.5 2.8 2.0 88.8 2.5

Stop Time: San Antonio, Texas
Emission Point: 1 Run #: 2 San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

210-623-1314

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 t 15 0:20:00 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified)

## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases Unit 1Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:20:15 (%) (ppm) (ppm) (ppm) 9.2 447.0 7.3 43.0 88.5 2.5 8.5 584.8 8.0 45.8 88.4 2.5 8.4 583.8 8.0 46.0 88.1 2.5 8.4 586.0 8.0 47.3 87.6 2.5 8.4 581.5 8.0 47.5 87.8 2.5 8.4 586.0 8.0 48.0 8.4 590.0 8.0 50.0 8.4 590.0 8.0 49.0 8.4 587.0 8.0 48.0 87.5 2.5 8.4 584.0 8.0 47.0 8.4 579.0 8.0 46.0 8.4 574.0 8.0 46.0 8.4 574.0 8.0 46.0 87.6 2.5 8.4 583.0 8.0 47.5

8.4 577.8 8.0 46.3 87.6 2.5 20.6 138.0 3.8 6.5 87.6 2.5 21.0 6.5 3.0 2.8 87.5 2.5 21.0 4.0 2.5 2.0 86.8 2.5

Stop Time: 210-623-1314 San Antonio, Texas 78252 San Antonio, Texas
Emission Point: 1 Run #: 3

Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 t 15 0:30:00 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified)

## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases Unit 1Client: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:15.0 18.5 36 4 11 15 88.8 00:30.0 9.1 361 7 44 51 89 00:45.0 8.6 543 7 47 54 89.3 01:00.0 8.5 582 8 48 56 89.3 01:15.0 8.4 589 8 50 58 89.7 01:30.0 8.4 598 8 52 60 89.7 01:45.0 8.4 602 8 51 59 89.7 02:00.0 8.4 592 8 47 55 90 02:15.0 8.4 583 8 47 55 89.6 02:30.0 8.4 584 8 48 56 89.7 02:45.0 8.4 586 8 48 56 89.9 03:00.0 8.4 587 8 49 57 90 03:15.0 8.4 588 8 48 56 90.2 03:30.0 8.4 589 8 49 57 90.3 03:45.0 8.4 590 8 49 57 90.3 04:00.0 8.4 589 8 48 56 89.9 04:15.0 8.4 588 8 48 56 89.9 04:30.0 8.4 588 8 50 58 90.1 04:45.0 8.4 591 8 50 58 90 05:00.0 8.4 590 8 49 57 89.7 05:15.0 8.4 587 8 49 57 89.5 05:30.0 8.4 587 8 49 57 89.2 05:45.0 8.4 585 8 47 55 88.9 06:00.0 8.4 584 8 49 57 89.2 06:15.0 8.4 584 8 49 57 89.1 06:30.0 8.4 583 8 48 56 89 06:45.0 8.4 581 8 47 55 88.8 07:00.0 8.4 581 8 48 56 88.5 07:15.0 19.1 444 5 16 21 88.5 07:30.0 20.8 117 4 6 10 88.4 07:45.0 20.9 36 3 4 7 88.4 08:00.0 21 18 3 3 6 88.3 08:15.0 21 10 3 3 6 88.3 08:30.0 21 8 3 3 6 88.4 08:45.0 21 7 3 3 6 88.5 09:00.0 21 6 3 3 6 89.1 09:15.0 21 5 3 3 6 89.3 09:30.0 21 5 3 2 5 89.2 09:45.0 21 4 3 2 5 89.2 10:00.0 21 4 2 2 4 89.3 August 27, 2009 Caterpillar G 3520-C; E-1 Energy Developments San Antonio, Texas

48 56 89.0 test phase

average 8.4 584 8

ed-09-sanantonio.tx-ecom# 3 -gases Unit 1Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:15.0 11 128 5 35 40 89 10:30.0 8.7 491 7 44 51 88.9 10:45.0 8.5 568 7 45 52 88.9 11:00.0 8.5 589 8 46 54 88.9 11:15.0 8.5 590 8 46 54 88.8 11:30.0 8.5 592 8 46 54 89 11:45.0 8.5 591 8 46 54 89.3 12:00.0 8.5 590 8 46 54 89.4 12:15.0 8.4 589 8 46 54 89.7 12:30.0 8.4 588 8 47 55 89.9 12:45.0 8.4 589 8 47 55 89.9 13:00.0 8.4 582 8 46 54 89.9 13:15.0 8.4 578 8 45 53 89.8 13:30.0 8.4 578 8 45 53 89.7 13:45.0 8.4 579 8 49 57 89.6 14:00.0 8.4 591 8 49 57 89.7 14:15.0 8.4 591 8 49 57 89.7 14:30.0 8.4 590 8 49 57 89.7 14:45.0 8.4 589 8 48 56 89.7 15:00.0 8.4 586 8 47 55 89.7 15:15.0 8.4 583 8 47 55 89.7 15:30.0 8.4 578 8 46 54 89.8 15:45.0 8.4 576 8 47 55 90 16:00.0 8.4 577 8 47 55 89.9 16:15.0 8.4 582 8 48 56 89.5 16:30.0 8.4 585 8 49 57 89.4 16:45.0 8.4 587 8 50 58 89.3 17:00.0 8.4 589 8 50 58 89.1 17:15.0 18.1 517 6 22 28 89.2 17:30.0 20.7 140 4 7 11 89.3 17:45.0 20.9 40 3 4 7 89.4 18:00.0 21 19 3 3 6 89.3 18:15.0 21 11 3 3 6 89.3 18:30.0 21 8 3 3 6 89.3 18:45.0 21 6 3 3 6 89 19:00.0 21 6 3 3 6 88.9 19:15.0 21 5 3 2 5 89 19:30.0 21 5 3 2 5 88.9 19:45.0 21 4 3 2 5 88.7 20:00.0 21 4 2 2 4 88.6 Energy Developments August 27, 2009 San Antonio, Texas Caterpillar G 3520-C; E-1

8 48 56 89.6 test phase

average 8.4 582

ed-09-sanantonio.tx-ecom# 3 -gases Unit 1Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:15.0 11 138 6 36 42 88.5 20:30.0 8.8 496 7 44 51 88.5 20:45.0 8.5 570 8 46 54 88.5 21:00.0 8.5 584 8 46 54 88.5 21:15.0 8.5 586 8 46 54 88.5 21:30.0 8.5 585 8 46 54 88.5 21:45.0 8.5 585 8 46 54 88.3 22:00.0 8.4 583 8 45 53 88.3 22:15.0 8.4 582 8 45 53 88.1 22:30.0 8.4 583 8 45 53 88.1 22:45.0 8.4 584 8 46 54 88.2 23:00.0 8.4 586 8 48 56 88.1 23:15.0 8.4 589 8 48 56 87.5 23:30.0 8.4 588 8 47 55 87.6 23:45.0 8.4 584 8 47 55 87.7 24:00.0 8.4 583 8 47 55 87.7 24:15.0 8.4 581 8 47 55 87.7 24:30.0 8.4 579 8 47 55 87.9 24:45.0 8.4 580 8 48 56 88 25:00.0 8.4 586 8 48 56 87.7 25:15.0 8.4 586 8 48 56 87.7 25:30.0 8.4 590 8 50 58 87.5 25:45.0 8.4 590 8 49 57 87.5 26:00.0 8.4 587 8 48 56 87.3 26:15.0 8.4 584 8 47 55 87.7 26:30.0 8.4 579 8 46 54 87.7 26:45.0 8.4 574 8 46 54 87.5 27:00.0 8.4 574 8 46 54 87.4 27:15.0 19.4 401 5 14 19 87.5 27:30.0 20.8 102 4 5 9 87.6 27:45.0 21 33 3 4 7 87.6 28:00.0 21 16 3 3 6 87.7 28:15.0 21 9 3 3 6 87.6 28:30.0 21 7 3 3 6 87.6 28:45.0 21 5 3 3 6 87.5 29:00.0 21 5 3 2 5 87.3 29:15.0 21 5 3 2 5 87.2 29:30.0 21 4 3 2 5 87 29:45.0 21 4 2 2 4 86.7 30:00.0 21 3 2 2 4 86.4 August 27, 2009 San Antonio, Texas Caterpillar G 3520-C; E-1 Energy Developments

48 56 87.5 test phase

average 8.4 583 8

ed-09-sanantonio.tx-ecom# 3 -gases Unit 1

# TEST RESULTS AND CALCULATIONS Unit 2 Emissions DataLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:00:11 (%) (ppm) (ppm) (ppm) 8.4 627.8 9.0 45.3 92.6 2.5 8.4 634.3 9.0 47.0 92.8 2.5 8.4 632.3 9.0 46.8 92.7 2.5 8.4 628.5 9.0 45.8 92.5 2.5 8.4 628.3 9.0 46.5 92.5 2.5 8.4 629.0 9.0 46.0 8.4 628.0 9.0 46.0 8.4 627.0 9.0 46.0 8.3 629.0 9.0 47.0 92.8 2.5 8.3 629.0 9.0 46.0 8.3 629.0 9.0 46.0 8.4 629.0 9.0 46.0 8.4 628.0 9.0 45.0 92.5 2.5 8.4 628.5 9.0 46.0

8.4 628.8 9.0 45.8 92.5 2.5 19.9 203.5 4.0 10.0 92.5 2.5 21.0 8.5 3.0 3.5 92.3 2.5 21.0 4.5 2.5 3.0 91.6 2.5

Stop Time:

Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Emission Point: 2 Run #:

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314

Date: 8/27/2009

t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Source Test

RAMPUP PHASE Cell Temp Flow Rate

t 8

t 10 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:15

0:09:56 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 t 13

## REFRESH PHASE t 9

t 14 t 15 t 7 1

9121OCVNXH San Antonio, Texas

t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes Sample Flow Rate are within specifications (±10% or as verified)

ed-09-sanantonio.tx-ecom# 3 -gases Unit 2Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:10:11 (%) (ppm) (ppm) (ppm) 12.0 353.3 5.5 31.8 91.5 2.5 8.4 628.5 7.8 44.5 91.8 2.5 8.3 632.8 8.8 44.8 92.1 2.5 8.4 624.0 9.0 42.3 92.2 2.5 8.4 621.5 9.3 42.5 92.4 2.5 8.3 624.0 10.0 44.0 8.4 623.0 9.0 43.0 8.4 622.0 9.0 43.0 8.4 622.0 9.0 43.0 92.3 2.5 8.4 620.0 9.0 43.0 8.3 621.0 9.0 44.0 8.3 622.0 9.0 44.0 8.3 620.0 9.0 43.0 92.2 2.5 8.4 621.8 9.1 43.4

8.3 620.8 9.0 43.5 92.2 2.5 19.9 202.3 4.0 9.3 92.2 2.5 21.0 7.5 3.0 3.0 91.9 2.5 21.0 4.3 3.0 3.0 91.2 2.5

Stop Time: San Antonio, Texas
Emission Point: 2 Run #: 2 San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

210-623-1314

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 t 15 0:19:56 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified)

## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases Unit 2Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:20:11 (%) (ppm) (ppm) (ppm) 10.2 418.5 6.8 38.3 91.3 2.5 8.4 629.3 8.5 44.0 91.8 2.5 8.4 624.5 9.3 43.5 92.3 2.5 8.4 624.3 10.0 44.0 92.4 2.5 8.4 621.3 10.0 44.0 92.1 2.5 8.4 614.0 10.0 42.0 8.4 614.0 10.0 44.0 8.3 616.0 10.0 45.0 8.3 620.0 10.0 45.0 92.0 2.5 8.3 620.0 10.0 45.0 8.3 620.0 10.0 45.0 8.3 621.0 10.0 44.0 8.3 621.0 10.0 46.0 91.6 2.5 8.3 618.3 10.0 44.5

8.3 620.5 10.0 45.0 91.6 2.5 19.5 223.0 4.5 11.5 91.7 2.5 21.0 8.3 3.0 3.0 91.5 2.5 21.0 4.3 3.0 2.8 90.9 2.5

Stop Time: 210-623-1314 San Antonio, Texas 78252 San Antonio, Texas
Emission Point: 2 Run #: 3

Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 t 15 0:29:56 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified)

## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases Unit 2Client: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:11.0 8.4 627 9 45 54 92.2 00:26.0 8.4 628 9 45 54 92.4 00:41.0 8.4 627 9 45 54 92.9 00:56.0 8.4 629 9 46 55 92.8 01:11.0 8.4 632 9 47 56 92.8 01:26.0 8.4 635 9 47 56 92.9 01:41.0 8.4 635 9 47 56 92.7 01:56.0 8.4 635 9 47 56 92.8 02:11.0 8.4 635 9 47 56 92.9 02:26.0 8.4 633 9 46 55 92.6 02:41.0 8.4 630 9 47 56 92.6 02:56.0 8.4 631 9 47 56 92.7 03:11.0 8.4 632 9 47 56 92.5 03:26.0 8.4 631 9 46 55 92.6 03:41.0 8.4 626 9 45 54 92.5 03:56.0 8.4 625 9 45 54 92.3 04:11.0 8.4 625 9 46 55 92.2 04:26.0 8.4 628 9 47 56 92.4 04:41.0 8.4 630 9 46 55 92.5 04:56.0 8.4 630 9 47 56 92.7 05:11.0 8.4 629 9 46 55 92.8 05:26.0 8.4 628 9 46 55 93 05:41.0 8.4 627 9 46 55 92.8 05:56.0 8.3 629 9 47 56 92.7 06:11.0 8.3 629 9 46 55 92.8 06:26.0 8.3 629 9 46 55 92.4 06:41.0 8.4 629 9 46 55 92.4 06:56.0 8.4 628 9 45 54 92.3 07:11.0 17.4 578 6 23 29 92.4 07:26.0 20.6 166 4 8 12 92.4 07:41.0 20.8 49 3 5 8 92.6 07:56.0 20.9 21 3 4 7 92.5 08:11.0 20.9 12 3 4 7 92.5 08:26.0 20.9 9 3 4 7 92.5 08:41.0 21 7 3 3 6 92.3 08:56.0 21 6 3 3 6 91.9 09:11.0 21 5 3 3 6 92 09:26.0 21 5 3 3 6 91.6 09:41.0 21 4 2 3 5 91.3 09:56.0 21 4 2 3 5 91.5 August 27, 2009 Caterpillar G 3520-C; E-2 Energy Developments San Antonio, Texas

46 55 92.7 test phase

average 8.4 629 9

ed-09-sanantonio.tx-ecom# 3 -gases Unit 2Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:11.0 21 4 2 3 5 91.4 10:26.0 9.8 240 6 36 42 91.4 10:41.0 8.6 551 7 43 50 91.5 10:56.0 8.4 618 7 45 52 91.6 11:11.0 8.4 628 7 45 52 91.7 11:26.0 8.4 629 8 44 52 91.9 11:41.0 8.4 628 8 44 52 91.8 11:56.0 8.4 629 8 45 53 91.7 12:11.0 8.3 630 8 45 53 91.9 12:26.0 8.3 634 9 46 55 92 12:41.0 8.3 635 9 45 54 92.1 12:56.0 8.4 632 9 43 52 92.4 13:11.0 8.4 626 9 42 51 92.1 13:26.0 8.4 623 9 42 51 92.1 13:41.0 8.4 624 9 43 52 92.2 13:56.0 8.4 623 9 42 51 92.4 14:11.0 8.4 621 9 42 51 92.5 14:26.0 8.4 620 9 42 51 92.5 14:41.0 8.4 622 9 43 52 92.4 14:56.0 8.4 623 10 43 53 92.3 15:11.0 8.3 624 10 44 54 92.2 15:26.0 8.4 623 9 43 52 92.3 15:41.0 8.4 622 9 43 52 92.3 15:56.0 8.4 622 9 43 52 92.3 16:11.0 8.4 620 9 43 52 92.2 16:26.0 8.3 621 9 44 53 92.3 16:41.0 8.3 622 9 44 53 92.1 16:56.0 8.3 620 9 43 52 92.1 17:11.0 17.3 579 6 22 28 92.1 17:26.0 20.6 162 4 7 11 92.2 17:41.0 20.8 48 3 4 7 92.2 17:56.0 20.9 20 3 4 7 92.2 18:11.0 20.9 11 3 3 6 92 18:26.0 20.9 8 3 3 6 92 18:41.0 21 6 3 3 6 91.9 18:56.0 21 5 3 3 6 91.7 19:11.0 21 5 3 3 6 91.5 19:26.0 21 4 3 3 6 91.3 19:41.0 21 4 3 3 6 91 19:56.0 21 4 3 3 6 91.1 Energy Developments August 27, 2009 San Antonio, Texas Caterpillar G 3520-C; E-2

9 43 53 92.2 test phase

average 8.4 622

ed-09-sanantonio.tx-ecom# 3 -gases Unit 2Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:11.0 15 4 4 21 25 91 20:26.0 8.9 446 7 43 50 91.1 20:41.0 8.5 600 8 44 52 91.3 20:56.0 8.5 624 8 45 53 91.6 21:11.0 8.4 630 8 46 54 91.6 21:26.0 8.4 633 8 45 53 91.8 21:41.0 8.4 630 9 43 52 91.9 21:56.0 8.4 624 9 42 51 92 22:11.0 8.4 623 9 44 53 92.2 22:26.0 8.3 625 9 44 53 92.2 22:41.0 8.3 625 9 43 52 92.3 22:56.0 8.4 625 10 43 53 92.3 23:11.0 8.4 625 10 44 54 92.4 23:26.0 8.4 624 10 44 54 92.4 23:41.0 8.4 624 10 44 54 92.4 23:56.0 8.4 624 10 44 54 92.3 24:11.0 8.4 621 10 44 54 92.2 24:26.0 8.3 622 10 45 55 92.1 24:41.0 8.3 623 10 44 54 92.1 24:56.0 8.4 619 10 43 53 92.1 25:11.0 8.4 614 10 42 52 92.1 25:26.0 8.4 614 10 44 54 92.2 25:41.0 8.3 616 10 45 55 91.9 25:56.0 8.3 620 10 45 55 91.7 26:11.0 8.3 620 10 45 55 91.7 26:26.0 8.3 620 10 45 55 91.7 26:41.0 8.3 621 10 44 54 91.4 26:56.0 8.3 621 10 46 56 91.6 27:11.0 15.8 616 7 29 36 91.4 27:26.0 20.5 200 4 8 12 91.6 27:41.0 20.8 55 4 5 9 91.8 27:56.0 20.9 21 3 4 7 91.8 28:11.0 20.9 12 3 3 6 91.7 28:26.0 21 8 3 3 6 91.7 28:41.0 21 7 3 3 6 91.4 28:56.0 21 6 3 3 6 91.3 29:11.0 21 5 3 3 6 91.1 29:26.0 21 4 3 3 6 91 29:41.0 21 4 3 3 6 90.9 29:56.0 21 4 3 2 5 90.7 August 27, 2009 San Antonio, Texas Caterpillar G 3520-C; E-2 Energy Developments

45 55 91.8 test phase

average 8.3 618 10

ed-09-sanantonio.tx-ecom# 3 -gases Unit 2

# TEST RESULTS AND CALCULATIONS Unit 3 Emissions DataLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:00:09 (%) (ppm) (ppm) (ppm) 8.5 515.0 8.0 38.5 90.5 2.5 8.5 515.8 8.0 39.8 91.1 2.5 8.5 512.8 8.0 39.5 90.7 2.5 8.5 512.5 8.8 39.8 90.2 2.5 8.5 513.8 9.0 40.8 90.0 2.5 8.5 515.0 9.0 42.0 8.5 516.0 9.0 41.0 8.4 515.0 9.0 41.0 8.4 516.0 9.0 42.0 90.2 2.5 8.5 515.0 9.0 41.0 8.5 512.0 9.0 40.0 8.5 510.0 9.0 40.0 8.5 508.0 9.0 39.0 90.1 2.5 8.5 513.4 9.0 40.8

8.5 511.3 9.0 40.0 90.1 2.5 19.7 176.0 4.3 9.5 90.4 2.5 21.0 6.8 3.0 3.0 90.3 2.5 21.0 3.5 3.0 2.0 90.2 2.5

Stop Time: t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes t 13

## REFRESH PHASE t 9

t 14 t 15 1

9121OCVNXH San Antonio, Texas

t 7 t 8

t 10 t 5:15

Sample Flow Rate are within specifications (±10% or as verified) 0:09:54 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Source Test

RAMPUP PHASE Cell Temp Flow Rate San Antonio, Texas 78252 210-623-1314 ECOM-AC Analyzer make & model: Emission Point: 3 Run #:

t 2 Calibration Gas Information

Date: 8/27/2009 Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ed-09-sanantonio.tx-ecom# 3 -gases Unit 3Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:10:09 (%) (ppm) (ppm) (ppm) 10.1 348.3 7.0 32.3 89.5 2.5 8.5 517.5 8.0 38.5 89.5 2.5 8.5 513.8 8.8 38.5 88.6 2.5 8.5 513.5 9.0 39.3 89.0 2.5 8.5 515.5 9.0 40.3 89.0 2.5 8.5 511.0 9.0 38.0 8.5 508.0 9.0 38.0 8.5 508.0 9.0 38.0 8.5 508.0 9.0 39.0 89.1 2.5 8.5 510.0 9.0 41.0 8.5 513.0 9.0 41.0 8.5 513.0 9.0 41.0 8.5 513.0 9.0 41.0 89.3 2.5 8.5 510.5 9.0 39.6

8.5 512.3 9.0 41.0 89.3 2.5 19.4 187.5 4.5 10.3 89.0 2.5 21.0 7.0 3.0 2.5 89.4 2.5 21.0 3.8 2.8 1.8 89.0 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:19:54 Average Concentration (t5:15 - t7:00)



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH 210-623-1314 San Antonio, Texas
Emission Point: 3 Run #: 2

ed-09-sanantonio.tx-ecom# 3 -gases Unit 3Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:20:09 (%) (ppm) (ppm) (ppm) 10.2 344.0 6.8 31.3 88.7 2.5 8.5 512.3 8.0 37.5 88.5 2.5 8.5 516.0 8.5 39.3 88.2 2.5 8.5 513.3 9.0 39.0 88.3 2.5 8.5 510.5 9.0 39.8 88.8 2.5 8.5 513.0 9.0 41.0 8.5 513.0 9.0 40.0 8.5 512.0 9.0 41.0 8.5 512.0 9.0 40.0 88.9 2.5 8.5 510.0 9.0 39.0 8.5 508.0 9.0 40.0 8.5 510.0 9.0 41.0 8.5 511.0 9.0 41.0 89.3 2.5 8.5 511.1 9.0 40.4

8.5 509.8 9.0 40.3 89.3 2.5 19.2 189.0 4.5 10.5 88.7 2.5 21.0 7.0 3.0 2.5 88.0 2.5 21.0 3.5 3.0 1.5 87.2 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:29:54 Average Concentration (t5:15 - t7:00)



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Emission Point: 3 Run #: 3
210-623-1314

ed-09-sanantonio.tx-ecom# 3- gases Unit 3Client: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:09.0 8.5 517 8 38 46 90.8 00:24.0 8.5 516 8 39 47 90.5 00:39.0 8.5 513 8 38 46 90.3 00:54.0 8.5 514 8 39 47 90.5 01:09.0 8.5 515 8 39 47 90.8 01:24.0 8.5 515 8 39 47 90.9 01:39.0 8.4 516 8 40 48 91.4 01:54.0 8.5 517 8 41 49 91.1 02:09.0 8.5 515 8 39 47 90.9 02:24.0 8.5 511 8 39 47 90.7 02:39.0 8.5 511 8 40 48 90.5 02:54.0 8.5 514 8 40 48 90.5 03:09.0 8.5 513 8 40 48 90.3 03:24.0 8.5 514 9 40 49 90.1 03:39.0 8.5 512 9 39 48 90.1 03:54.0 8.5 511 9 40 49 90.1 04:09.0 8.5 512 9 40 49 90 04:24.0 8.5 513 9 41 50 89.9 04:39.0 8.5 515 9 41 50 89.9 04:54.0 8.5 515 9 41 50 90 05:09.0 8.5 515 9 42 51 90.1 05:24.0 8.5 516 9 41 50 90.1 05:39.0 8.4 515 9 41 50 90.3 05:54.0 8.4 516 9 42 51 90.3 06:09.0 8.5 515 9 41 50 90.2 06:24.0 8.5 512 9 40 49 90.1 06:39.0 8.5 510 9 40 49 90 06:54.0 8.5 508 9 39 48 90.2 07:09.0 16.4 494 6 24 30 90.3 07:24.0 20.6 151 4 7 11 90.5 07:39.0 20.9 42 4 4 8 90.5 07:54.0 21 17 3 3 6 90.4 08:09.0 21 10 3 3 6 90.3 08:24.0 21 7 3 3 6 90.1 08:39.0 21 5 3 3 6 90.3 08:54.0 21 5 3 3 6 90.4 09:09.0 21 4 3 2 5 90.4 09:24.0 21 4 3 2 5 90.3 09:39.0 21 3 3 2 5 90.1 09:54.0 21 3 3 2 5 89.9
50 90.2 test phase

average 8.5 513 9 41 August 27, 2009 Caterpillar G 3520-C; E-3 Energy Developments San Antonio, Texas

ed-09-sanantonio.tx-ecom# 3 -gases Unit 3Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:09.0 14 12 5 18 23 89.3 10:24.0 9 379 7 35 42 89.5 10:39.0 8.6 491 8 38 46 89.6 10:54.0 8.6 511 8 38 46 89.5 11:09.0 8.5 515 8 39 47 89.5 11:24.0 8.5 521 8 39 47 89.7 11:39.0 8.5 520 8 38 46 89.5 11:54.0 8.5 514 8 38 46 89.3 12:09.0 8.5 514 8 39 47 88.7 12:24.0 8.5 515 9 39 48 88.5 12:39.0 8.5 513 9 38 47 88.5 12:54.0 8.5 513 9 38 47 88.6 13:09.0 8.5 513 9 38 47 89.1 13:24.0 8.5 512 9 39 48 89.2 13:39.0 8.5 514 9 40 49 88.9 13:54.0 8.5 515 9 40 49 88.7 14:09.0 8.5 515 9 40 49 88.8 14:24.0 8.5 516 9 41 50 88.9 14:39.0 8.5 516 9 41 50 88.9 14:54.0 8.5 515 9 39 48 89.5 15:09.0 8.5 511 9 38 47 89.6 15:24.0 8.5 508 9 38 47 89.3 15:39.0 8.5 508 9 38 47 89 15:54.0 8.5 508 9 39 48 88.6 16:09.0 8.5 510 9 41 50 89.1 16:24.0 8.5 513 9 41 50 89.2 16:39.0 8.5 513 9 41 50 89.3 16:54.0 8.5 513 9 41 50 89.5 17:09.0 14.8 512 7 27 34 89.5 17:24.0 20.6 171 4 7 11 89.3 17:39.0 21 48 4 4 8 88.8 17:54.0 21 19 3 3 6 88.5 18:09.0 21 10 3 3 6 89.3 18:24.0 21 7 3 3 6 89.4 18:39.0 21 6 3 2 5 89.5 18:54.0 21 5 3 2 5 89.5 19:09.0 21 4 3 2 5 89.3 19:24.0 21 4 3 2 5 88.9 19:39.0 21 4 3 2 5 88.8 19:54.0 21 3 2 1 3 89.1
511 9 40 49 89.2 test phase

average 8.5 San Antonio, Texas Caterpillar G 3520-C; E-3 Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases Unit 3Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:09.0 14.4 7 4 18 22 88.8 20:24.0 9 376 7 34 41 88.8 20:39.0 8.6 485 8 36 44 88.6 20:54.0 8.6 508 8 37 45 88.6 21:09.0 8.5 510 8 37 45 88.5 21:24.0 8.5 513 8 37 45 88.5 21:39.0 8.5 513 8 38 46 88.6 21:54.0 8.5 513 8 38 46 88.2 22:09.0 8.5 512 8 38 46 88.4 22:24.0 8.5 516 8 40 48 88.2 22:39.0 8.5 518 9 40 49 88 22:54.0 8.5 518 9 39 48 88.1 23:09.0 8.5 515 9 39 48 88.3 23:24.0 8.5 515 9 40 49 88.4 23:39.0 8.5 513 9 39 48 88.1 23:54.0 8.5 510 9 38 47 88.2 24:09.0 8.5 509 9 39 48 88.3 24:24.0 8.5 510 9 39 48 88.8 24:39.0 8.5 511 9 40 49 89.1 24:54.0 8.5 512 9 41 50 89 25:09.0 8.5 513 9 41 50 88.9 25:24.0 8.5 513 9 40 49 88.7 25:39.0 8.5 512 9 41 50 88.9 25:54.0 8.5 512 9 40 49 88.9 26:09.0 8.5 510 9 39 48 89 26:24.0 8.5 508 9 40 49 89.3 26:39.0 8.5 510 9 41 50 89.4 26:54.0 8.5 511 9 41 50 89.4 27:09.0 14.4 511 7 28 35 89.1 27:24.0 20.5 177 4 7 11 88.6 27:39.0 21 49 4 4 8 88.5 27:54.0 21 19 3 3 6 88.4 28:09.0 21 10 3 3 6 88.3 28:24.0 21 7 3 3 6 88.1 28:39.0 21 6 3 2 5 87.9 28:54.0 21 5 3 2 5 87.8 29:09.0 21 4 3 2 5 87.6 29:24.0 21 4 3 2 5 87.2 29:39.0 21 3 3 1 4 87.1 29:54.0 21 3 3 1 4 86.9
511 9 40 49 89.1 test phase

average 8.5 San Antonio, Texas Caterpillar G 3520-C; E-3 Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases Unit 3

# TEST RESULTS AND CALCULATIONS Unit 4 Emissions DataLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:00:13 (%) (ppm) (ppm) (ppm) 8.6 556.5 8.0 38.0 85.9 2.5 8.5 555.0 9.0 38.5 87.2 2.5 8.5 554.5 9.0 38.8 88.0 2.5 8.5 554.0 9.0 40.0 88.3 2.5 8.5 553.0 9.0 40.0 88.2 2.5 8.5 553.0 9.0 40.0 8.5 553.0 9.0 40.0 8.5 552.0 9.0 41.0 8.5 552.0 9.0 41.0 87.4 2.5 8.5 550.0 9.0 40.0 8.5 550.0 9.0 41.0 8.5 552.0 9.0 42.0 8.5 553.0 9.0 41.0 86.0 2.5 8.5 551.9 9.0 40.8

8.5 551.3 9.0 41.0 86.0 2.5 20.4 154.8 3.8 7.0 85.6 2.5 21.0 6.8 2.5 2.3 85.2 2.5 21.0 3.8 2.0 1.8 83.2 2.5

Stop Time:

Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Emission Point: 4 Run #:

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314

Date: 8/27/2009

t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Source Test

RAMPUP PHASE Cell Temp Flow Rate

t 8

t 10 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:15

0:09:59 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 t 13

## REFRESH PHASE t 9

t 14 t 15 t 7 1

9121OCVNXH San Antonio, Texas

t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes Sample Flow Rate are within specifications (±10% or as verified)

ed-09-sanantonio.tx-ecom# 3 -gases Unit 4Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:10:14 (%) (ppm) (ppm) (ppm) 9.4 405.0 6.0 34.5 84.1 2.5 8.6 556.0 7.0 39.5 85.1 2.5 8.5 557.5 8.3 40.0 85.4 2.5 8.5 557.3 9.0 39.0 86.6 2.5 8.5 553.5 9.0 39.0 86.8 2.5 8.5 552.0 9.0 39.0 8.5 553.0 9.0 39.0 8.5 552.0 9.0 39.0 8.5 552.0 9.0 39.0 86.1 2.5 8.5 552.0 9.0 40.0 8.5 553.0 9.0 40.0 8.5 554.0 9.0 40.0 8.5 552.0 9.0 39.0 86.0 2.5 8.5 552.5 9.0 39.4

8.5 552.8 9.0 39.8 86.0 2.5 20.5 149.3 3.5 6.3 85.8 2.5 21.0 6.8 2.3 2.3 86.0 2.5 21.0 3.8 2.0 2.0 85.4 2.5

Stop Time: San Antonio, Texas
Emission Point: 4 Run #: 2 San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

210-623-1314

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 t 15 0:19:58 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified)

## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases Unit 4Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:20:13 (%) (ppm) (ppm) (ppm) 9.2 418.3 6.0 36.3 85.6 2.5 8.6 554.3 7.0 40.3 85.1 2.5 8.5 550.0 7.3 39.3 84.7 2.5 8.5 550.8 8.3 39.3 84.1 2.5 8.5 551.0 9.0 38.5 83.8 2.5 8.5 549.0 9.0 38.0 8.5 548.0 9.0 38.0 8.5 549.0 9.0 38.0 8.5 548.0 9.0 38.0 83.8 2.5 8.5 548.0 9.0 38.0 8.5 547.0 9.0 38.0 8.5 547.0 9.0 39.0 8.5 549.0 9.0 39.0 83.5 2.5 8.5 548.1 9.0 38.3

8.5 547.8 9.0 38.5 83.5 2.5 20.2 162.0 3.5 7.0 84.0 2.5 21.0 7.0 2.0 2.3 84.0 2.5 21.0 4.3 2.0 2.0 87.8 2.5

Stop Time: 210-623-1314 San Antonio, Texas 78252 San Antonio, Texas
Emission Point: 4 Run #: 3

Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 t 15 0:29:58 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified)

## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases Unit 4Client: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:13.0 8.6 559 8 38 46 85.6 00:28.0 8.6 558 8 38 46 85.7 00:43.0 8.6 555 8 38 46 86 00:59.0 8.5 554 8 38 46 86.3 01:13.0 8.5 556 9 39 48 86.7 01:28.0 8.5 556 9 38 47 87.1 01:44.0 8.5 554 9 38 47 87.3 01:58.0 8.5 554 9 39 48 87.5 02:13.0 8.5 555 9 39 48 87.7 02:29.0 8.5 554 9 38 47 88 02:43.0 8.5 554 9 39 48 88.1 02:58.0 8.5 555 9 39 48 88.1 03:13.0 8.5 554 9 39 48 88.3 03:28.0 8.5 553 9 40 49 88.3 03:43.0 8.5 554 9 41 50 88.3 03:59.0 8.5 555 9 40 49 88.3 04:14.0 8.5 554 9 40 49 88.3 04:28.0 8.5 553 9 40 49 88.3 04:43.0 8.5 552 9 40 49 88.2 04:58.0 8.5 553 9 40 49 88.1 05:13.0 8.5 553 9 40 49 87.9 05:28.0 8.5 553 9 40 49 87.7 05:43.0 8.5 552 9 41 50 87.3 05:58.0 8.5 552 9 41 50 86.7 06:13.0 8.5 550 9 40 49 86.4 06:28.0 8.5 550 9 41 50 86.2 06:43.0 8.5 552 9 42 51 85.9 06:59.0 8.5 553 9 41 50 85.6 07:14.0 18.7 449 5 16 21 85.5 07:29.0 20.8 118 4 5 9 85.5 07:44.0 21 36 3 4 7 85.7 07:58.0 21 16 3 3 6 85.8 08:13.0 21 9 3 3 6 85.6 08:29.0 21 7 3 2 5 85.5 08:43.0 21 6 2 2 4 85 08:58.0 21 5 2 2 4 84.6 09:13.0 21 4 2 2 4 84.1 09:28.0 21 4 2 2 4 82.9 09:43.0 21 4 2 2 4 82.7 09:59.0 21 3 2 1 3 83 August 27, 2009 Caterpillar G 3520-C; E-4 Energy Developments San Antonio, Texas

41 50 86.7 test phase

average 8.5 552 9

ed-09-sanantonio.tx-ecom# 3 -gases Unit 4Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:14.0 11.5 93 4 26 30 83.4 10:28.0 8.9 448 6 35 41 84 10:44.0 8.6 531 7 38 45 84.4 10:58.0 8.6 548 7 39 46 84.6 11:13.0 8.6 554 7 39 46 84.9 11:28.0 8.6 556 7 39 46 85.1 11:43.0 8.5 557 7 40 47 85.2 11:58.0 8.5 557 7 40 47 85.1 12:13.0 8.5 557 8 40 48 85.1 12:29.0 8.5 557 8 40 48 85.4 12:43.0 8.5 558 8 40 48 85.5 12:58.0 8.5 558 9 40 49 85.5 13:13.0 8.5 559 9 39 48 86 13:28.0 8.5 557 9 39 48 86.7 13:44.0 8.5 557 9 39 48 86.9 13:58.0 8.5 556 9 39 48 86.9 14:13.0 8.5 554 9 39 48 87.1 14:28.0 8.5 553 9 39 48 86.9 14:44.0 8.5 554 9 39 48 86.7 14:58.0 8.5 553 9 39 48 86.5 15:14.0 8.5 552 9 39 48 86.1 15:28.0 8.5 553 9 39 48 86.1 15:43.0 8.5 552 9 39 48 86.2 15:58.0 8.5 552 9 39 48 86.1 16:13.0 8.5 552 9 40 49 86.1 16:28.0 8.5 553 9 40 49 86 16:43.0 8.5 554 9 40 49 85.9 16:58.0 8.5 552 9 39 48 85.9 17:14.0 19 432 5 14 19 85.8 17:29.0 20.8 113 3 5 8 85.7 17:43.0 21 36 3 3 6 85.7 17:58.0 21 16 3 3 6 86 18:13.0 21 9 3 3 6 86 18:28.0 21 7 2 2 4 86 18:43.0 21 6 2 2 4 86 18:58.0 21 5 2 2 4 85.8 19:13.0 21 4 2 2 4 85.7 19:28.0 21 4 2 2 4 85.4 19:43.0 21 4 2 2 4 85.2 19:58.0 21 3 2 2 4 85.3 Energy Developments August 27, 2009 San Antonio, Texas Caterpillar G 3520-C; E-4

9 39 48 86.1 test phase

average 8.5 553

ed-09-sanantonio.tx-ecom# 3 -gases Unit 4Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:13.0 10.9 132 5 28 33 85.5 20:28.0 8.8 458 6 37 43 85.7 20:43.0 8.6 534 6 39 45 85.6 20:59.0 8.6 549 7 41 48 85.5 21:14.0 8.6 556 7 41 48 85.3 21:29.0 8.6 555 7 40 47 85.1 21:43.0 8.5 553 7 40 47 85.1 21:58.0 8.5 553 7 40 47 85 22:13.0 8.5 552 7 39 46 84.9 22:28.0 8.5 549 7 39 46 84.7 22:43.0 8.5 549 7 39 46 84.6 22:58.0 8.5 550 8 40 48 84.5 23:13.0 8.5 551 8 39 47 84.3 23:28.0 8.5 550 8 39 47 84.1 23:44.0 8.5 550 8 39 47 84 23:59.0 8.5 552 9 40 49 83.8 24:14.0 8.5 552 9 39 48 83.8 24:29.0 8.5 551 9 38 47 83.7 24:44.0 8.5 551 9 39 48 83.7 24:59.0 8.5 550 9 38 47 83.9 25:13.0 8.5 549 9 38 47 83.9 25:28.0 8.5 548 9 38 47 83.8 25:43.0 8.5 549 9 38 47 83.8 25:58.0 8.5 548 9 38 47 83.7 26:13.0 8.5 548 9 38 47 83.6 26:28.0 8.5 547 9 38 47 83.6 26:43.0 8.5 547 9 39 48 83.5 26:58.0 8.5 549 9 39 48 83.4 27:13.0 18.2 469 5 16 21 83.5 27:28.0 20.8 124 3 5 8 84.2 27:43.0 20.9 38 3 4 7 84.2 27:58.0 21 17 3 3 6 84.1 28:13.0 21 10 2 3 5 84.1 28:28.0 21 7 2 2 4 84 28:44.0 21 6 2 2 4 83.9 28:58.0 21 5 2 2 4 83.8 29:13.0 21 5 2 2 4 86.9 29:28.0 21 4 2 2 4 87.1 29:43.0 21 4 2 2 4 88.6 29:58.0 21 4 2 2 4 88.7 August 27, 2009 San Antonio, Texas Caterpillar G 3520-C; E-4 Energy Developments

38 47 83.7 test phase

average 8.5 548 9

ed-09-sanantonio.tx-ecom# 3 -gases Unit 4

# TEST RESULTS AND CALCULATIONS Unit 5 Emissions DataLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:00:00 (%) (ppm) (ppm) (ppm) 8.3 571.5 8.8 48.0 96.1 2.5 8.3 570.8 9.0 48.0 97.4 2.5 8.3 572.3 9.0 49.8 98.3 2.5 8.3 572.8 9.0 50.3 98.7 2.5 8.3 569.8 9.0 50.0 99.1 2.5 8.3 569.0 10.0 51.0 8.2 574.0 10.0 52.0 8.3 574.0 10.0 52.0 8.3 573.0 10.0 52.0 98.6 2.5 8.3 573.0 10.0 52.0 8.3 573.0 10.0 52.0 8.3 571.0 10.0 52.0 8.3 570.0 10.0 51.0 98.1 2.5 8.3 572.1 10.0 51.8

8.3 571.8 10.0 51.8 98.1 2.5 17.3 270.3 5.8 20.0 97.4 2.5 20.8 9.3 3.0 4.3 97.3 2.5 20.9 4.8 3.0 3.0 96.7 2.5

Stop Time: t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes t 13

## REFRESH PHASE t 9

t 14 t 15 1

9121OCVNXH San Antonio, Texas

t 7 t 8

t 10 t 5:15

Sample Flow Rate are within specifications (±10% or as verified) 0:09:46 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Source Test

RAMPUP PHASE Cell Temp Flow Rate San Antonio, Texas 78252 210-623-1314 ECOM-AC Analyzer make & model: Emission Point: 5 Run #:

t 2 Calibration Gas Information

Date: 8/27/2009 Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ed-09-sanantonio.tx-ecom# 3 -gases Unit 5Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:10:00 (%) (ppm) (ppm) (ppm) 12.1 295.0 6.5 33.0 96.4 2.5 8.3 568.3 9.3 49.3 96.4 2.5 8.3 571.0 10.0 50.0 96.6 2.5 8.3 566.5 10.5 49.5 97.1 2.5 8.3 564.0 11.0 49.3 96.8 2.5 8.3 562.0 11.0 48.0 8.3 560.0 11.0 48.0 8.3 557.0 11.0 48.0 8.3 560.0 11.0 50.0 97.2 2.5 8.3 563.0 11.0 50.0 8.2 566.0 12.0 53.0 8.1 580.0 12.0 56.0 8.1 591.0 12.0 57.0 97.6 2.5 8.2 567.4 11.4 51.3

8.2 575.0 11.8 54.0 97.6 2.5 17.3 269.5 6.8 21.5 98.3 2.5 20.8 9.3 4.0 4.3 98.6 2.5 20.9 4.5 3.0 3.0 98.8 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:19:45 Average Concentration (t5:15 - t7:00)



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH 210-623-1314 San Antonio, Texas
Emission Point: 5 Run #: 2

ed-09-sanantonio.tx-ecom# 3 -gases Unit 5Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:20:00 (%) (ppm) (ppm) (ppm) 12.1 301.0 6.5 34.5 99.0 2.5 8.3 564.3 9.0 50.3 99.5 2.5 8.3 565.3 9.0 51.0 100.4 2.5 8.3 564.3 9.5 50.8 100.5 2.5 8.3 556.8 10.0 50.3 100.9 2.5 8.3 560.0 10.0 51.0 8.3 559.0 10.0 51.0 8.3 556.0 10.0 50.0 8.3 555.0 10.0 50.0 100.9 2.5 8.3 556.0 10.0 51.0 8.3 561.0 10.0 52.0 8.3 564.0 10.0 52.0 8.3 561.0 10.0 51.0 101.7 2.5 8.3 559.0 10.0 51.0

8.3 560.5 10.0 51.5 101.7 2.5 17.3 266.5 6.3 20.0 101.2 2.5 20.9 9.3 4.0 3.8 100.2 2.5 21.0 4.8 3.0 3.0 98.5 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:29:45 Average Concentration (t5:15 - t7:00)



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Emission Point: 5 Run #: 3
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases Unit 5Client: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:00.0 8.4 567 8 46 54 96 00:16.0 8.3 569 9 48 57 96 00:31.0 8.3 575 9 49 58 96.1 00:45.0 8.3 575 9 49 58 96.4 01:01.0 8.3 574 9 48 57 96.8 01:15.0 8.3 572 9 48 57 97.4 01:30.0 8.3 569 9 48 57 97.6 01:46.0 8.3 568 9 48 57 97.8 02:00.0 8.3 568 9 48 57 98 02:15.0 8.3 570 9 50 59 98.4 02:30.0 8.3 575 9 51 60 98.4 02:45.0 8.3 576 9 50 59 98.4 03:00.0 8.3 573 9 50 59 98.5 03:15.0 8.3 573 9 50 59 98.6 03:31.0 8.3 573 9 51 60 98.8 03:45.0 8.3 572 9 50 59 98.8 04:01.0 8.3 571 9 50 59 99 04:15.0 8.3 571 9 50 59 99.1 04:30.0 8.3 569 9 50 59 99 04:45.0 8.3 568 9 50 59 99.1 05:00.0 8.3 569 10 51 61 99 05:15.0 8.2 574 10 52 62 98.8 05:31.0 8.3 574 10 52 62 98.3 05:46.0 8.3 573 10 52 62 98.2 06:00.0 8.3 573 10 52 62 98.2 06:15.0 8.3 573 10 52 62 98.3 06:30.0 8.3 571 10 52 62 98.2 06:45.0 8.3 570 10 51 61 97.5 07:00.0 8.3 568 10 51 61 97.2 07:16.0 19.4 382 5 17 22 97.3 07:31.0 20.7 98 4 7 11 97.4 07:45.0 20.8 33 4 5 9 97.6 08:00.0 20.8 15 3 5 8 97.3 08:15.0 20.8 9 3 4 7 97.2 08:30.0 20.8 7 3 4 7 97.3 08:45.0 20.9 6 3 4 7 97.3 09:01.0 20.9 5 3 3 6 97.4 09:15.0 20.9 5 3 3 6 95.9 09:30.0 20.9 5 3 3 6 96.7 09:46.0 20.9 4 3 3 6 96.6
62 98.3 test phase

average 8.3 572 10 52 August 27, 2009 Caterpillar G 3520-C; E-5 Energy Developments San Antonio, Texas

ed-09-sanantonio.tx-ecom# 3 -gases Unit 5Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:00.0 20.9 4 3 3 6 96.6 10:15.0 10.5 143 6 36 42 96.6 10:30.0 8.5 484 8 46 54 96.4 10:45.0 8.4 549 9 47 56 96 11:00.0 8.3 565 9 49 58 96.2 11:15.0 8.3 569 9 49 58 96.6 11:30.0 8.3 569 9 49 58 96.5 11:45.0 8.3 570 10 50 60 96.4 12:00.0 8.2 573 10 51 61 96.3 12:15.0 8.3 573 10 50 60 96.6 12:30.0 8.3 570 10 50 60 96.7 12:45.0 8.3 568 10 49 59 96.9 13:01.0 8.3 566 10 49 59 97 13:15.0 8.3 564 10 50 60 97.3 13:30.0 8.2 568 11 50 61 97 13:45.0 8.3 568 11 49 60 97 14:00.0 8.3 565 11 49 60 97 14:15.0 8.3 563 11 49 60 97 14:30.0 8.3 564 11 50 61 96.5 14:45.0 8.3 564 11 49 60 96.8 15:00.0 8.3 562 11 48 59 97.1 15:15.0 8.3 560 11 48 59 97.2 15:30.0 8.3 557 11 48 59 97.2 15:45.0 8.3 560 11 50 61 97.2 16:00.0 8.3 563 11 50 61 97.3 16:15.0 8.2 566 12 53 65 97.5 16:30.0 8.1 580 12 56 68 97.7 16:46.0 8.1 591 12 57 69 98 17:01.0 8.1 593 12 58 70 98.3 17:16.0 19.7 364 6 16 22 98.3 17:30.0 20.7 90 5 7 12 98.3 17:45.0 20.8 31 4 5 9 98.3 18:00.0 20.8 15 4 5 9 98.4 18:16.0 20.8 9 4 4 8 98.6 18:31.0 20.8 7 4 4 8 98.7 18:46.0 20.9 6 4 4 8 98.7 19:00.0 20.9 5 3 3 6 99 19:15.0 20.9 5 3 3 6 98.8 19:31.0 20.9 4 3 3 6 98.6 19:45.0 20.9 4 3 3 6 98.6
567 11 51 63 97.4 test phase

average 8.2 San Antonio, Texas Caterpillar G 3520-C; E-5 Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases Unit 5Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:00.0 21 3 3 3 6 99.1 20:15.0 10.2 171 7 38 45 98.8 20:30.0 8.6 483 8 47 55 99.1 20:45.0 8.4 547 8 50 58 99.1 21:00.0 8.3 564 9 51 60 99.4 21:15.0 8.3 564 9 50 59 99.3 21:30.0 8.3 565 9 50 59 99.6 21:45.0 8.3 564 9 50 59 99.7 22:00.0 8.3 565 9 51 60 100.2 22:15.0 8.3 566 9 50 59 100.3 22:30.0 8.3 563 9 51 60 100.4 22:45.0 8.3 567 9 52 61 100.5 23:00.0 8.3 567 9 51 60 100.6 23:15.0 8.3 565 9 51 60 100.4 23:30.0 8.3 563 10 51 61 100.6 23:45.0 8.3 562 10 50 60 100.5 24:00.0 8.3 556 10 49 59 100.7 24:15.0 8.3 555 10 50 60 100.8 24:30.0 8.3 557 10 51 61 101 24:45.0 8.3 559 10 51 61 101.1 25:00.0 8.3 560 10 51 61 101 25:15.0 8.3 559 10 51 61 100.9 25:30.0 8.3 556 10 50 60 100.7 25:45.0 8.3 555 10 50 60 101 26:00.0 8.3 556 10 51 61 101.4 26:15.0 8.3 561 10 52 62 101.6 26:30.0 8.3 564 10 52 62 101.8 26:45.0 8.3 561 10 51 61 101.8 27:00.0 8.3 561 10 51 61 101 27:15.0 19.5 377 6 17 23 101.2 27:30.0 20.7 97 5 7 12 101.6 27:45.0 20.8 31 4 5 9 101 28:00.0 20.9 15 4 4 8 100.8 28:16.0 20.9 9 4 4 8 100.5 28:30.0 20.9 7 4 4 8 99.9 28:45.0 20.9 6 4 3 7 99.6 29:00.0 20.9 5 3 3 6 99.1 29:15.0 20.9 5 3 3 6 98.9 29:31.0 21 5 3 3 6 97.7 29:45.0 21 4 3 3 6 98.1
559 10 51 61 101.3 test phase

average 8.3 San Antonio, Texas Caterpillar G 3520-C; E-5 Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases Unit 5

# TEST RESULTS AND CALCULATIONS Unit 6 Emissions DataLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:00:11 (%) (ppm) (ppm) (ppm) 8.6 490.0 9.0 38.3 93.5 2.5 8.5 490.0 9.0 38.8 92.8 2.5 8.6 491.8 9.3 38.5 91.6 2.5 8.6 494.8 10.0 39.3 92.8 2.5 8.5 503.5 10.0 42.0 93.7 2.5 8.5 502.0 10.0 41.0 8.5 501.0 10.0 40.0 8.6 499.0 10.0 41.0 8.6 499.0 10.0 41.0 96.1 2.5 8.6 496.0 10.0 41.0 8.6 494.0 10.0 39.0 8.7 490.0 10.0 35.0 8.8 485.0 10.0 34.0 96.3 2.5 8.6 495.8 10.0 39.0

8.7 491.3 10.0 37.3 96.3 2.5 20.3 142.5 5.0 7.8 96.1 2.5 21.0 6.8 3.8 2.5 96.3 2.5 21.0 4.3 3.0 1.3 96.1 2.5

Stop Time: t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes t 13

## REFRESH PHASE t 9

t 14 t 15 1

9121OCVNXH San Antonio, Texas

t 7 t 8

t 10 t 5:15

Sample Flow Rate are within specifications (±10% or as verified) 0:09:57 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Source Test

RAMPUP PHASE Cell Temp Flow Rate San Antonio, Texas 78252 210-623-1314 ECOM-AC Analyzer make & model: Emission Point: 6 Run #:

t 2 Calibration Gas Information

Date: 8/27/2009 Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ed-09-sanantonio.tx-ecom# 3 -gases Unit 6Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:10:12 (%) (ppm) (ppm) (ppm) 10.0 338.5 7.0 33.0 96.2 2.5 8.6 494.8 8.0 39.0 94.8 2.5 8.6 496.8 8.8 40.3 95.9 2.5 8.6 500.0 9.0 40.5 95.6 2.5 8.6 497.3 9.0 40.0 96.4 2.5 8.6 502.0 9.0 42.0 8.6 502.0 9.0 41.0 8.6 499.0 9.0 41.0 8.6 497.0 9.0 41.0 96.4 2.5 8.6 496.0 9.0 40.0 8.6 496.0 9.0 40.0 8.6 496.0 9.0 40.0 8.6 495.0 9.0 40.0 96.7 2.5 8.6 497.9 9.0 40.6

8.6 495.8 9.0 40.0 96.7 2.5 20.2 150.5 4.8 8.0 95.6 2.5 21.0 6.8 3.3 2.5 95.4 2.5 21.0 4.3 3.0 1.8 95.7 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:19:56 Average Concentration (t5:15 - t7:00)



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH 210-623-1314 San Antonio, Texas
Emission Point: 6 Run #: 2

ed-09-sanantonio.tx-ecom# 3 -gases Unit 6Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration

O 2 CO NO NO 2 Start time: 0:20:11 (%) (ppm) (ppm) (ppm) 9.7 356.3 7.0 35.5 94.7 2.5 8.7 498.0 8.0 39.3 94.5 2.5 8.6 501.0 9.0 40.5 95.2 2.5 8.6 506.8 9.8 43.0 96.6 2.5 8.8 497.0 10.0 40.8 97.3 2.5 8.8 490.0 9.0 37.0 8.7 486.0 9.0 38.0 8.7 486.0 9.0 37.0 8.7 485.0 9.0 36.0 98.3 2.5 8.6 485.0 10.0 36.0 8.5 490.0 10.0 39.0 8.5 500.0 11.0 41.0 8.5 505.0 11.0 42.0 97.7 2.5 8.6 490.9 9.8 38.3

8.5 495.0 10.5 39.5 97.7 2.5 20.2 153.0 4.8 8.5 97.0 2.5 21.0 7.3 3.0 2.8 97.2 2.5 21.0 4.3 3.0 2.0 95.9 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:29:57 Average Concentration (t5:15 - t7:00)



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Source Test

Flow Rate Date: 8/27/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Emission Point: 6 Run #: 3
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases Unit 6Client: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:11.0 8.6 493 9 39 48 93.8 00:27.0 8.6 491 9 38 47 93.5 00:42.0 8.6 488 9 38 47 93.3 00:57.0 8.6 488 9 38 47 93.2 01:12.0 8.5 488 9 38 47 93.3 01:27.0 8.5 488 9 39 48 92.9 01:41.0 8.5 491 9 39 48 92.7 01:56.0 8.5 493 9 39 48 92.2 02:11.0 8.5 493 9 39 48 91.3 02:26.0 8.6 492 9 39 48 91.3 02:41.0 8.7 491 9 35 44 91.6 02:56.0 8.5 491 10 41 51 92 03:11.0 8.5 496 10 41 51 91.9 03:26.0 8.6 498 10 37 47 93.7 03:41.0 8.6 491 10 39 49 92.9 03:56.0 8.5 494 10 40 50 92.5 04:11.0 8.5 500 10 42 52 93.1 04:27.0 8.5 505 10 42 52 93.5 04:41.0 8.5 505 10 42 52 93.9 04:56.0 8.5 504 10 42 52 94.2 05:11.0 8.5 502 10 41 51 95.4 05:27.0 8.5 501 10 40 50 96.4 05:42.0 8.6 499 10 41 51 96.4 05:57.0 8.6 499 10 41 51 96 06:12.0 8.6 496 10 41 51 96.2 06:26.0 8.6 494 10 39 49 95.4 06:41.0 8.7 490 10 35 45 96.4 06:56.0 8.8 485 10 34 44 97.2 07:11.0 18.5 412 7 18 25 96.8 07:26.0 20.8 110 5 6 11 96 07:42.0 21 33 4 4 8 96.1 07:56.0 21 15 4 3 7 95.6 08:12.0 21 9 4 3 7 95.7 08:26.0 21 7 4 3 7 96.3 08:41.0 21 6 4 2 6 96.4 08:57.0 21 5 3 2 5 96.6 09:11.0 21 5 3 2 5 96.7 09:26.0 21 4 3 1 4 96.2 09:41.0 21 4 3 1 4 96 09:57.0 21 4 3 1 4 95.5
49 96.2 test phase

average 8.6 496 10 39 August 27, 2009 Caterpillar G 3520-C; E-6 Energy Developments San Antonio, Texas

ed-09-sanantonio.tx-ecom# 3 -gases Unit 6Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:12.0 13.5 20 5 21 26 95.8 10:26.0 9 374 7 35 42 96.2 10:41.0 8.7 471 8 38 46 96.1 10:56.0 8.7 489 8 38 46 96.6 11:11.0 8.7 491 8 38 46 94.6 11:26.0 8.6 494 8 39 47 94.6 11:41.0 8.6 497 8 40 48 95 11:56.0 8.6 497 8 39 47 95 12:11.0 8.6 496 8 39 47 95.5 12:26.0 8.6 496 9 40 49 95.8 12:42.0 8.6 496 9 40 49 96.2 12:56.0 8.6 499 9 42 51 96.1 13:11.0 8.6 502 9 42 51 96.2 13:26.0 8.6 502 9 41 50 95.6 13:41.0 8.6 500 9 40 49 95.5 13:56.0 8.6 496 9 39 48 95.2 14:11.0 8.6 495 9 39 48 95.8 14:27.0 8.6 497 9 40 49 96.3 14:41.0 8.6 498 9 40 49 96.3 14:57.0 8.6 499 9 41 50 97.2 15:11.0 8.6 502 9 42 51 96.8 15:26.0 8.6 502 9 41 50 96.4 15:42.0 8.6 499 9 41 50 95.9 15:57.0 8.6 497 9 41 50 96.4 16:12.0 8.6 496 9 40 49 96.6 16:26.0 8.6 496 9 40 49 96.7 16:41.0 8.6 496 9 40 49 96.7 16:57.0 8.6 495 9 40 49 96.8 17:11.0 18.2 432 6 19 25 96.2 17:26.0 20.8 119 5 6 11 95.8 17:41.0 20.9 35 4 4 8 95.4 17:56.0 21 16 4 3 7 95 18:11.0 21 9 4 3 7 95.5 18:27.0 21 7 3 3 6 95.6 18:41.0 21 6 3 2 5 95.4 18:56.0 21 5 3 2 5 95.2 19:12.0 21 5 3 2 5 95.5 19:26.0 21 4 3 2 5 95.5 19:41.0 21 4 3 2 5 95.9 19:56.0 21 4 3 1 4 95.8
498 9 41 50 96.5 test phase

average 8.6 San Antonio, Texas Caterpillar G 3520-C; E-6 Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases Unit 6Company: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:11.0 12.4 51 5 24 29 95.8 20:26.0 9 394 7 37 44 95 20:41.0 8.7 481 8 41 49 94.5 20:56.0 8.7 499 8 40 48 93.5 21:11.0 8.7 498 8 38 46 94.1 21:26.0 8.7 495 8 39 47 94.3 21:42.0 8.6 499 8 40 48 95 21:56.0 8.6 500 8 40 48 94.6 22:11.0 8.6 500 9 40 49 94.8 22:26.0 8.6 499 9 40 49 94.7 22:42.0 8.6 501 9 41 50 95.6 22:56.0 8.6 504 9 41 50 95.8 23:11.0 8.6 505 9 41 50 96.6 23:26.0 8.6 506 10 44 54 96.5 23:41.0 8.6 509 10 44 54 96.7 23:56.0 8.7 507 10 43 53 96.4 24:11.0 8.7 501 10 42 52 96 24:27.0 8.7 499 10 42 52 97.2 24:41.0 8.8 496 10 40 50 97.8 24:56.0 8.8 492 10 39 49 98 25:11.0 8.8 490 9 37 46 98.8 25:26.0 8.7 486 9 38 47 98.1 25:41.0 8.7 486 9 37 46 98.1 25:56.0 8.7 485 9 36 45 98 26:12.0 8.6 485 10 36 46 97.8 26:26.0 8.5 490 10 39 49 97.6 26:41.0 8.5 500 11 41 52 97.8 26:56.0 8.5 505 11 42 53 97.6 27:11.0 18.2 440 6 19 25 97.3 27:26.0 20.7 118 5 7 12 96.4 27:41.0 20.9 37 4 4 8 96.5 27:56.0 21 17 4 4 8 97.8 28:11.0 21 10 3 3 6 97.8 28:27.0 21 7 3 3 6 97.2 28:41.0 21 6 3 3 6 97 28:56.0 21 6 3 2 5 96.6 29:12.0 21 5 3 2 5 96.3 29:26.0 21 4 3 2 5 95.9 29:41.0 21 4 3 2 5 95.8 29:57.0 21 4 3 2 5 95.7
491 10 38 48 98.0 test phase

average 8.6 San Antonio, Texas Caterpillar G 3520-C; E-6 Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases Unit 6

# APPENDIX B UNIT OPERATION PARAMETERS

### Client: Location:

Phone: Project #: Analyzer make & model: Serial #: Repeatability Date: Test Date: Repeatability Gas type O2 % CO ppm NO ppm NO2 ppm Concentration 20.9 897 124 48
Calibration Gas type O2 % CO ppm NO ppm NO2 ppm Concentration 20.9 897 124 48
Emission Point 1 2 3 4 5 6 Caterpillar G3520-C; E-5 Caterpillar G3520-C; E-6 Address:

Unit ed-09-sanantonio.tx-ecom#2

Caterpillar G3520-C; E-2 Energy Developments San Antonio, Texas 8611 Covel Road San Antonio, Texas 78252 210-623-1314
ECOM-AC

Caterpillar G3520-C; E-3 Caterpillar G3520-C; E-4 8/26/2009 8/27/2009 9121OCVNXH

Caterpillar G3520-C; E-1

ed-09-sanantonio.tx-ecom# 3 -gases Info

### 123456 Air Fuel Ratio 27.90 26.50 26.20 27.30 27.70 27.40 Engine Speed (rpm) 1200 1200 1200 1200 1200 1200 Load (kW) 1450 1502 1600 1600 1600 1500 Exhaust Temp ( o 

### F) 644 640 645 635 643 645 Brake Horsepower (hp) 2211 2211 2211 2211 2211 2211 Unit Number 

# ENGINE OPERATING DATA SUMMARY May 28, 2009

# APPENDIX C CALIBRATION GAS CERTIFICATIONS

# APPENDIX D QUALITY ASSURANCE AND QUALITY CONTROL DATA

## ed-09-sanantonio.tx-ecom#3-rpt 

## QA/QC PROGRAM Air Hygiene ensures the quality and validity of its emission meas urement and reporting procedures through a rigorous quality assurance (QA) program. The program is developed and administer ed by an internal QA team and encompasses five major areas: 1. QA reviews of reports, labo ratory work, and field testing 2. Equipment calibration and maintenance 3. Chain-of-custody 4. Training 5. Knowledge of current test methods Each of these areas is discussed individually below. QA Reviews Air Hygiene’s review procedure includes revi ew of each source test report, along with la boratory and fieldwork, by the QA Team. The most important review is the one that takes place before a test program begins. The QA Team works closely with technical division personnel to prepare and review test protocols. Test protocol review includes selection of appropriate test procedure s, evaluation of interferences or other restrictions that might preclude use of standard test procedures, and evaluation and/or de velopment of alternate procedures. Equipment Calibration and Maintenance The equipment used to conduct the emission measurements is ma intained according to the manufactur er’s instructions to ensure proper operation. In addition to the maintenance program, calibrations ar e carried out on each measurement device according to the schedule outlined by the Environmental Protection Agency. Quality control checks are also conducted in the field for each test program. Chain-of-Custody Air Hygiene maintains full chain-of-custody documentation on all samples and data sheets. In addition to normal documentation of changes between field sample custodians, laboratory personnel, and field test personnel, Air Hygiene documents every individual who handles any test component in the field (e .g., probe wash, impinger loading and recove ry, filter loading and recovery, etc.). Samples are stored in a locked area to which only Air Hygiene personnel have access. Field data sheets are secured at Air Hygiene’s of fices upon return from the field. Training Personnel’s training is essential to ensure quality testing. Air Hygiene has formal and informal training programs, which incl ude: 1. Attendance at EPA-sponsored training courses 2. Enrollment in EPA correspondence courses 3 A requirement for all technicians to re ad and understand Air Hygiene’s QA manual 4. In-house training and QA meetings on a regular basis 5. Maintenance of training records Knowledge of Current Test Methods With the constant updating of standard test methods and the wide variety of emerging test procedures, it is essential that any qualified source tester keep abreast of new developm ents. Air Hygiene subscribes to services, which provide updates on EPA reference methods, rules, and regulations. Additionally, source test personn el regularly attend and present papers at testing and emissi on-related seminars and conferences. Air Hygiene personnel maintain memb ership in the Air and Waste Management Association and the American Industrial Hygiene Association.

## ed-09-sanantonio.tx-ecom#3-rpt 

## COMBUSTION TESTING QUAL ITY ASSURANCE ACTIVITIES A number of quality assurance activities were undertaken before, dur ing, and after this testing project. This section of the r eport combined with the documentation in Appendix C describe each of those activities. Each instrument’s response was checked and adjusted in the field prior to the collection of data via multi-point calibration. The instrument’s linearity was checked by adjusting its zero and span responses to zero nitrogen an d an upscale calibration gas in the range of the expected concentrations. The instru ment response was then challenged with other calibration gases of known concentratio n and accepted as being linear if the response of the other calibration ga ses agreed within plus or mi nus two percent of the range of predicted values. NO 2 

### to NO conversion was checked via direct connect with an EPA Protocol certified concentration of NO 2 

### in a balance of nitrogen. Conversion was verified to be between 90 and 110 percent. After each test run, the analyzers were chec ked for zero and span drift. This allowe d each test run to be bracketed by calibra tions and documents the precision of the data just co llected. The criterion for acceptable data is that the instrument drift is no more than three percent of the full-scale response. The quality assurance worksheets in the following pages summarize all multipoint calibrati on checks and zero to span checks pe rformed during the tests. These worksheets (as prepared from the data records of Appendix A) show that no drifts in excess of three percent occurre d in the zero to span check s following each test run. The sampling systems were leak checked by demonstrating that a vacuum greater than 10 in Hg could be held for at least one minu te with a decline of less than one in. Hg. A leak test was conduct ed after the sample system was set up and before the system was dismantled. This test was conducted to ensure that ambient air had not diluted the sample. Any leakage detected prior to the tests would be repaired and another leak check conducted before testing commenced. No leaks were found during the pre or post-test l eak checks. The absence of leaks in the sampling system was also verified by a sampling system bi as check. The sampling system’s integrity was tested by comparing the responses of the analyzers to the calibration gases introduced via two paths. The first path was direc tly into the analyzer and the second path via the sample system at the sample probe. An y difference in the instru ment responses by thes e two methods was attributed to sampli ng system bias or leakage. Th e criterion for acceptance is agreem ent within five percent of th e span of the analyzer. The control gases used to calibrate the instruments were analyzed and certified by the compressed gas vendors to plus or minus one percent accuracy for all gases. EPA Protocol No. 1 was used, wh ere applicable to assign the co ncentration values traceable to the National Institute of Standards and Technology (NIST), Standard Reference Materials (SRM’s). The gas calibration sheets as prepared by the vendor are contained in Appendix C. Air Hygiene collected and reported the enclosed test data in accordance with the procedures and quality assurance activities de scribed in this test report. Air Hygiene makes no warranty as to the suitability of the test methods. Air Hygiene also assumes no lia bility relating to the interpretation and use of the test data.

INSTRUMENTAL ANALYSIS QUALITY ASSURANCE DATA 

## Date: August 27, 2009 Company: Energy Development, Inc. Location: San Antonio, Texas Techs: NA Sample System Leak Check 

## Date Sample System Leak Rate (l/min) August 27, 2009 1 0Location:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 897

O 2 CO NO NO 2 Start time: 0:00:00 (%) (ppm) (ppm) (ppm) 6.7 435.0 2.3 3.8 69.2 2.5 0.0 803.5 0.0 4.0 69.2 2.5 0.0 891.8 0.0 4.0 69.2 2.5 0.0 895.3 0.0 2.8 69.2 2.5 0.0 885.8 0.0 2.0 69.1 2.5 0.0 896.0 0.0 2.0 0.0 889.0 0.0 2.0 0.0 895.0 0.0 1.0 0.0 895.0 0.0 1.0 69.1 2.5 0.0 896.0 0.0 1.0 0.0 898.0 0.0 1.0 0.0 891.0 0.0 1.0 0.0 892.0 0.0 1.0 69.1 2.5 0.0 894.0 0.0 1.3 0.6% 

### Yes 0.3% 

### Yes 0.0 894.3 0.0 1.0 69.1 2.5 14.5 483.5 0.0 1.0 69.1 2.5 21.0 12.8 0.0 1.8 69.1 2.5 21.0 4.8 0.0 2.0 69.1 2.5

Stop Time:

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes Maximum Deviation (±2.0% or ±1 ppm)

Sample Flow Rate are within specifications (±10% or as verified) 0:09:45 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 t 13

## REFRESH PHASE t 9

t 14 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:15 t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Repeatability Test

RAMPUP PHASE Cell Temp Flow Rate Date: 8/26/2009 San Antonio, Texas 78252 210-623-1314 1 San Antonio, Texas

Analyzer make & model: Run #:

t 2 Calibration Gas Information 9121OCVNXH Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC

Acceptable Calibration Error t 7 t 8

t 10

t 15

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 897

O 2 CO NO NO 2 Start time: 0:10:00 (%) (ppm) (ppm) (ppm) 21.0 3.0 0.0 2.0 69.1 2.5 21.0 2.0 0.0 2.0 69.0 2.5 7.4 317.8 0.0 2.0 69.0 2.5 0.0 822.5 0.0 2.0 68.8 2.5 0.0 904.5 0.0 1.0 68.8 2.5 0.0 900.0 0.0 1.0 0.0 899.0 0.0 1.0 0.0 898.0 0.0 1.0 0.0 898.0 0.0 1.0 68.8 2.5 0.0 898.0 0.0 1.0 0.0 898.0 0.0 0.0 0.0 897.0 0.0 0.0 0.0 897.0 0.0 0.0 68.8 2.5 0.0 898.1 0.0 0.6 0.2% 

### Yes 0.1% 

### Yes 0.0 897.5 0.0 0.3 68.8 2.5 15.1 434.3 0.0 0.0 68.7 2.5 21.0 10.5 0.0 1.0 68.6 2.5 21.0 3.3 0.0 1.0 68.6 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:19:45 Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Run #: 2
210-623-1314 8611 Covel Road Address:

Calibration Gas Verification Information

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 897

O 2 CO NO NO 2 Start time: 0:20:00 (%) (ppm) (ppm) (ppm) 6.9 339.5 0.0 1.0 68.6 2.5 0.0 824.0 0.0 1.0 68.6 2.5 0.0 868.3 0.0 0.3 68.5 2.5 0.0 896.0 0.0 0.0 68.5 2.5 0.0 899.5 0.0 0.0 68.4 2.5 0.0 896.0 0.0 0.0 0.0 890.0 0.0 0.0 0.1 881.0 0.0 0.0 0.2 887.0 0.0 0.0 68.4 2.5 0.3 894.0 0.0 0.0 0.4 893.0 0.0 0.0 0.6 897.0 0.0 0.0 0.6 895.0 0.0 0.0 68.3 2.5 0.3 891.6 0.0 0.0 1.2% 

### Yes 0.6% 

### Yes 0.5 894.8 0.0 0.0 68.3 2.5 15.0 475.5 0.0 0.0 68.2 2.5 21.0 11.3 0.0 0.0 68.2 2.5 21.0 3.3 0.0 0.5 68.1 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:29:45 Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Run #: 3
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 897

O 2 CO NO NO 2 Start time: 0:30:00 (%) (ppm) (ppm) (ppm) 16.4 30.3 0.0 1.0 68.1 2.5 0.0 789.0 0.0 0.0 68.0 2.5 0.0 894.3 0.0 0.0 67.9 2.5 0.0 913.8 0.0 0.0 67.9 2.5 0.0 917.3 0.0 0.0 67.8 2.5 0.0 900.0 0.0 0.0 0.0 899.0 0.0 0.0 0.0 899.0 0.0 0.0 0.0 898.0 0.0 0.0 67.8 2.5 0.0 897.0 0.0 0.0 0.0 897.0 0.0 0.0 0.0 897.0 0.0 0.0 0.0 897.0 0.0 0.0 67.7 2.5 0.0 898.0 0.0 0.0 0.2% 

### Yes 0.1% 

### Yes 0.0 897.0 0.0 0.0 67.7 2.5 0.0 889.0 0.0 0.0 67.7 2.5 20.2 231.5 0.0 0.0 67.7 2.5 21.0 7.0 0.0 0.0 67.7 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:39:45 Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Run #: 4
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatClient: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:00.0 21 1 0 3 3 69.2 00:15.0 5.5 65 7 4 11 69.2 00:30.0 0.1 853 1 4 5 69.2 00:45.0 0 821 1 4 5 69.2 01:00.0 0 806 0 4 4 69.2 01:15.0 0 801 0 4 4 69.2 01:30.0 0 803 0 4 4 69.2 01:45.0 0 804 0 4 4 69.2 02:00.0 0 896 0 4 4 69.2 02:15.0 0 894 0 4 4 69.2 02:30.0 0 890 0 4 4 69.2 02:45.0 0 887 0 4 4 69.2 03:00.0 0 896 0 3 3 69.2 03:15.0 0 891 0 3 3 69.2 03:30.0 0 900 0 3 3 69.2 03:45.0 0 894 0 2 2 69.2 04:00.0 0 887 0 2 2 69.2 04:15.0 0 880 0 2 2 69.1 04:30.0 0 872 0 2 2 69.1 04:45.0 0 904 0 2 2 69.1 05:00.0 0 896 0 2 2 69.1 05:15.0 0 889 0 2 2 69.1 05:30.0 0 895 0 1 1 69.1 05:45.0 0 895 0 1 1 69.1 06:00.0 0 896 0 1 1 69.1 06:15.0 0 898 0 1 1 69.1 06:30.0 0 891 0 1 1 69.1 06:45.0 0 892 0 1 1 69.1 07:00.0 0 891 0 1 1 69.1 07:15.0 16.3 793 0 1 1 69.1 07:30.0 20.6 196 0 1 1 69.1 07:45.0 20.9 54 0 1 1 69.1 08:00.0 21 22 0 1 1 69.1 08:15.0 21 13 0 2 2 69.1 08:30.0 21 9 0 2 2 69.1 08:45.0 21 7 0 2 2 69.1 09:00.0 21 6 0 2 2 69.1 09:15.0 21 5 0 2 2 69.1 09:30.0 21 4 0 2 2 69.1 09:45.0 21 4 0 2 2 69.1
1 69.1 test phase

average 0.0 894 0 1 August 26, 2009 Energy Developments San Antonio, Texas

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:00.0 21 3 0 2 2 69.1 10:15.0 21 3 0 2 2 69.1 10:30.0 21 3 0 2 2 69.1 10:45.0 21 3 0 2 2 69.1 11:00.0 21 3 0 2 2 69.1 11:15.0 21 2 0 2 2 69 11:30.0 21 2 0 2 2 69 11:45.0 21 1 0 2 2 69 12:00.0 4.3 55 0 2 2 69 12:15.0 7.8 480 0 2 2 69 12:30.0 14.1 439 0 2 2 69 12:45.0 3.4 297 0 2 2 68.9 13:00.0 0 705 0 2 2 68.8 13:15.0 0 829 0 2 2 68.8 13:30.0 0 856 0 2 2 68.8 13:45.0 0 900 0 2 2 68.8 14:00.0 0 904 0 1 1 68.8 14:15.0 0 901 0 1 1 68.8 14:30.0 0 905 0 1 1 68.8 14:45.0 0 908 0 1 1 68.8 15:00.0 0 900 0 1 1 68.8 15:15.0 0 899 0 1 1 68.8 15:30.0 0 898 0 1 1 68.8 15:45.0 0 898 0 1 1 68.8 16:00.0 0 898 0 1 1 68.8 16:15.0 0 898 0 0 0 68.8 16:30.0 0 897 0 0 0 68.8 16:45.0 0 897 0 0 0 68.7 17:00.0 0 895 0 0 0 68.7 17:15.0 18.7 644 0 0 0 68.7 17:30.0 20.7 154 0 0 0 68.6 17:45.0 21 44 0 0 0 68.6 18:00.0 21 18 0 1 1 68.6 18:15.0 21 11 0 1 1 68.6 18:30.0 21 7 0 1 1 68.6 18:45.0 21 6 0 1 1 68.6 19:00.0 21 4 0 1 1 68.6 19:15.0 21 3 0 1 1 68.6 19:30.0 21 3 0 1 1 68.6 19:45.0 21 3 0 1 1 68.6
898 0 1 1 68.8 test phase

average 0.0 San Antonio, Texas Energy Developments August 26, 2009

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:00.0 21 2 0 1 1 68.6 20:15.0 6.4 17 0 1 1 68.6 20:30.0 0.1 579 0 1 1 68.6 20:45.0 0 760 0 1 1 68.6 21:00.0 0 805 0 1 1 68.6 21:15.0 0 823 0 1 1 68.6 21:30.0 0 831 0 1 1 68.6 21:45.0 0 837 0 1 1 68.5 22:00.0 0 843 0 1 1 68.5 22:15.0 0 850 0 0 0 68.5 22:30.0 0 886 0 0 0 68.5 22:45.0 0 894 0 0 0 68.5 23:00.0 0 893 0 0 0 68.5 23:15.0 0 898 0 0 0 68.5 23:30.0 0 895 0 0 0 68.4 23:45.0 0 898 0 0 0 68.4 24:00.0 0 899 0 0 0 68.4 24:15.0 0 900 0 0 0 68.4 24:30.0 0 900 0 0 0 68.4 24:45.0 0 899 0 0 0 68.4 25:00.0 0 896 0 0 0 68.4 25:15.0 0 890 0 0 0 68.4 25:30.0 0.1 881 0 0 0 68.3 25:45.0 0.2 887 0 0 0 68.3 26:00.0 0.3 894 0 0 0 68.3 26:15.0 0.4 893 0 0 0 68.3 26:30.0 0.6 897 0 0 0 68.2 26:45.0 0.6 895 0 0 0 68.2 27:00.0 0.7 897 0 0 0 68.2 27:15.0 17.5 762 0 0 0 68.2 27:30.0 20.7 189 0 0 0 68.2 27:45.0 21 54 0 0 0 68.2 28:00.0 21 21 0 0 0 68.2 28:15.0 21 11 0 0 0 68.2 28:30.0 21 7 0 0 0 68.2 28:45.0 21 6 0 0 0 68.2 29:00.0 21 4 0 0 0 68.1 29:15.0 21 4 0 0 0 68.1 29:30.0 21 3 0 1 1 68.1 29:45.0 21 2 0 1 1 68.2
892 0 0 0 68.3 test phase

average 0.3 San Antonio, Texas Energy Developments August 26, 2009

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 30:00.0 21 2 0 1 1 68.1 30:15.0 21 2 0 1 1 68.1 30:30.0 21 2 0 1 1 68.1 30:45.0 2.7 115 0 1 1 68.1 31:00.0 0 654 0 0 0 68 31:15.0 0 793 0 0 0 68 31:30.0 0 828 0 0 0 68 31:45.0 0 881 0 0 0 68 32:00.0 0 888 0 0 0 68 32:15.0 0 893 0 0 0 67.9 32:30.0 0 896 0 0 0 67.9 32:45.0 0 900 0 0 0 67.9 33:00.0 0 904 0 0 0 67.9 33:15.0 0 910 0 0 0 67.9 33:30.0 0 917 0 0 0 67.9 33:45.0 0 924 0 0 0 67.9 34:00.0 0 931 0 0 0 67.8 34:15.0 0 937 0 0 0 67.8 34:30.0 0 902 0 0 0 67.8 34:45.0 0 899 0 0 0 67.8 35:00.0 0 900 0 0 0 67.8 35:15.0 0 899 0 0 0 67.8 35:30.0 0 899 0 0 0 67.8 35:45.0 0 898 0 0 0 67.8 36:00.0 0 897 0 0 0 67.7 36:15.0 0 897 0 0 0 67.7 36:30.0 0 897 0 0 0 67.7 36:45.0 0 897 0 0 0 67.7 37:00.0 0 895 0 0 0 67.7 37:15.0 0 891 0 0 0 67.7 37:30.0 0 887 0 0 0 67.7 37:45.0 0 883 0 0 0 67.7 38:00.0 18.2 693 0 0 0 67.7 38:15.0 20.7 165 0 0 0 67.7 38:30.0 21 48 0 0 0 67.7 38:45.0 21 20 0 0 0 67.7 39:00.0 21 11 0 0 0 67.7 39:15.0 21 7 0 0 0 67.7 39:30.0 21 6 0 0 0 67.7 39:45.0 21 4 0 0 0 67.6
898 0 0 0 67.8 test phase

average 0.0 San Antonio, Texas Energy Developments August 26, 2009

ed-09-sanantonio.tx-ecom# 3 -gases CORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 124

O 2 CO NO NO 2 Start time: 0:00:00 (%) (ppm) (ppm) (ppm) 17.0 13.0 21.8 0.5 71.1 2.5 10.1 2.0 61.3 0.3 71.0 2.5 0.0 0.0 120.0 1.0 71.0 2.5 0.0 0.0 123.0 0.0 71.0 2.5 0.0 0.0 124.8 0.0 71.0 2.5 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 71.1 2.5 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 71.1 2.5 0.0 0.0 125.0 0.0 0.0% 

### Yes 0.8% 

### Yes 0.0 0.0 125.0 0.0 71.1 2.5 3.9 0.0 98.3 0.0 71.1 2.5 20.9 0.0 4.0 0.0 71.1 2.5 21.0 0.0 1.8 0.0 71.1 2.5

Stop Time:

Span Difference (±5.0% or ±1 ppm)

Acceptable Calibration Error t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes t 13

## REFRESH PHASE t 9

t 14 t 15 1

9121OCVNXH San Antonio, Texas

t 7 t 8

t 10 Maximum Deviation (±2.0% or ±1 ppm) Acceptable Test Data Phase t 5:15

Sample Flow Rate are within specifications (±10% or as verified) 0:09:45 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Repeatability Test

RAMPUP PHASE Cell Temp Flow Rate Date: 8/26/2009

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314 Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Run #:

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 124

O 2 CO NO NO 2 Start time: 0:10:00 (%) (ppm) (ppm) (ppm) 10.0 0.0 67.8 0.0 71.0 2.5 0.4 0.0 123.3 0.0 71.0 2.5 0.0 0.0 124.3 0.0 70.9 2.5 0.0 0.0 125.0 0.0 70.8 2.5 0.0 0.0 125.0 0.0 70.8 2.5 0.1 0.0 125.0 0.0 0.7 0.0 125.0 0.0 1.2 0.0 125.0 0.0 1.9 0.0 125.0 0.0 70.8 2.5 2.2 0.0 125.0 0.0 2.6 0.0 125.0 0.0 2.8 0.0 125.0 0.0 3.1 0.0 125.0 0.0 70.7 2.5 1.8 0.0 125.0 0.0 0.0% 

### Yes 0.8% 

### Yes 2.7 0.0 125.0 0.0 70.7 2.5 0.2 0.0 125.0 0.0 70.6 2.5 15.3 0.0 34.8 0.0 70.5 2.5 21.0 0.0 2.5 0.0 70.5 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:19:45 Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH 210-623-1314 San Antonio, Texas
Run #: 2

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 124

O 2 CO NO NO 2 Start time: 0:20:00 (%) (ppm) (ppm) (ppm) 7.7 0.0 77.8 0.0 70.4 2.5 0.0 0.0 123.8 0.0 70.4 2.5 0.0 0.0 124.0 0.0 70.4 2.5 0.0 0.0 124.5 0.0 70.3 2.5 0.0 0.0 125.0 0.0 70.3 2.5 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 70.2 2.5 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 70.2 2.5 0.0 0.0 125.0 0.0 0.0% 

### Yes 0.8% 

### Yes 0.0 0.0 125.0 0.0 70.2 2.5 3.8 0.0 98.5 0.0 70.3 2.5 20.9 0.0 4.8 0.0 70.3 2.5 21.0 0.0 2.3 0.0 70.2 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:29:45 Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Run #: 3
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 124

O 2 CO NO NO 2 Start time: 0:30:00 (%) (ppm) (ppm) (ppm) 8.0 0.0 80.5 0.0 70.2 2.5 0.0 0.0 124.0 0.0 70.2 2.5 0.0 0.0 124.0 0.0 70.2 2.5 0.0 0.0 124.8 0.0 70.2 2.5 0.0 0.0 125.0 0.0 70.2 2.5 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 70.3 2.5 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 70.2 2.5 0.0 0.0 125.0 0.0 0.0% 

### Yes 0.8% 

### Yes 0.0 0.0 125.0 0.0 70.2 2.5 14.9 0.0 37.8 0.0 70.3 2.5 21.0 0.0 3.3 0.0 70.3 2.5 21.0 0.0 2.0 0.0 70.3 2.5

Stop Time: Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes t 11 t 12 t 13 t 14 t 15 0:39:45 Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH San Antonio, Texas
Run #: 4
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatClient: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:00.0 21 2 0 0 0 71.1 00:15.0 5.9 12 81 0 81 71.1 00:30.0 20 28 4 1 5 71.1 00:45.0 20.9 10 2 1 3 71 01:00.0 21 4 1 0 1 71 01:15.0 19.1 2 25 0 25 71 01:30.0 0.4 1 99 0 99 71 01:45.0 0 1 120 1 121 71 02:00.0 0 0 120 1 121 71 02:15.0 0 0 120 1 121 71 02:30.0 0 0 120 1 121 71 02:45.0 0 0 120 1 121 71 03:00.0 0 0 120 0 120 71 03:15.0 0 0 124 0 124 71 03:30.0 0 0 124 0 124 71 03:45.0 0 0 124 0 124 71 04:00.0 0 0 124 0 124 71 04:15.0 0 0 125 0 125 71 04:30.0 0 0 125 0 125 71 04:45.0 0 0 125 0 125 71 05:00.0 0 0 125 0 125 71 05:15.0 0 0 125 0 125 71 05:30.0 0 0 125 0 125 71.1 05:45.0 0 0 125 0 125 71.1 06:00.0 0 0 125 0 125 71.1 06:15.0 0 0 125 0 125 71.1 06:30.0 0 0 125 0 125 71.1 06:45.0 0 0 125 0 125 71.1 07:00.0 0 0 125 0 125 71.1 07:15.0 0 0 125 0 125 71.1 07:30.0 0 0 125 0 125 71.1 07:45.0 15.4 0 18 0 18 71.1 08:00.0 20.7 0 6 0 6 71.1 08:15.0 21 0 4 0 4 71.1 08:30.0 21 0 3 0 3 71.1 08:45.0 21 0 3 0 3 71.1 09:00.0 21 0 2 0 2 71.1 09:15.0 21 0 2 0 2 71.1 09:30.0 21 0 2 0 2 71 09:45.0 21 0 1 0 1 71
125 71.1 test phase

average 0.0 0 125 0 August 26, 2009 Energy Developments San Antonio, Texas

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:00.0 21 0 1 0 1 71 10:15.0 18.7 0 31 0 31 71 10:30.0 0.3 0 118 0 118 71 10:45.0 0 0 121 0 121 71 11:00.0 1.7 0 121 0 121 71 11:15.0 0 0 124 0 124 71 11:30.0 0 0 124 0 124 71 11:45.0 0 0 124 0 124 71 12:00.0 0 0 124 0 124 71 12:15.0 0 0 124 0 124 70.9 12:30.0 0 0 124 0 124 70.9 12:45.0 0 0 125 0 125 70.9 13:00.0 0 0 125 0 125 70.9 13:15.0 0 0 125 0 125 70.8 13:30.0 0 0 125 0 125 70.8 13:45.0 0 0 125 0 125 70.8 14:00.0 0 0 125 0 125 70.8 14:15.0 0 0 125 0 125 70.8 14:30.0 0 0 125 0 125 70.8 14:45.0 0 0 125 0 125 70.8 15:00.0 0.1 0 125 0 125 70.8 15:15.0 0.7 0 125 0 125 70.8 15:30.0 1.2 0 125 0 125 70.8 15:45.0 1.9 0 125 0 125 70.7 16:00.0 2.2 0 125 0 125 70.7 16:15.0 2.6 0 125 0 125 70.7 16:30.0 2.8 0 125 0 125 70.6 16:45.0 3.1 0 125 0 125 70.6 17:00.0 0.7 0 125 0 125 70.6 17:15.0 0 0 125 0 125 70.6 17:30.0 0 0 125 0 125 70.6 17:45.0 0 0 125 0 125 70.6 18:00.0 0 0 125 0 125 70.5 18:15.0 19.4 0 5 0 5 70.5 18:30.0 20.9 0 5 0 5 70.5 18:45.0 21 0 4 0 4 70.5 19:00.0 21 0 3 0 3 70.5 19:15.0 21 0 3 0 3 70.5 19:30.0 21 0 2 0 2 70.5 19:45.0 21 0 2 0 2 70.5
0 125 0 125 70.7 test phase

average 1.8 San Antonio, Texas Energy Developments August 26, 2009

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:00.0 21 0 2 0 2 70.5 20:15.0 9.5 0 84 0 84 70.4 20:30.0 0.1 0 107 0 107 70.4 20:45.0 0 0 118 0 118 70.4 21:00.0 0 0 123 0 123 70.4 21:15.0 0 0 124 0 124 70.4 21:30.0 0 0 124 0 124 70.4 21:45.0 0 0 124 0 124 70.4 22:00.0 0 0 124 0 124 70.4 22:15.0 0 0 124 0 124 70.4 22:30.0 0 0 124 0 124 70.3 22:45.0 0 0 124 0 124 70.3 23:00.0 0 0 124 0 124 70.3 23:15.0 0 0 124 0 124 70.3 23:30.0 0 0 125 0 125 70.3 23:45.0 0 0 125 0 125 70.2 24:00.0 0 0 125 0 125 70.2 24:15.0 0 0 125 0 125 70.3 24:30.0 0 0 125 0 125 70.3 24:45.0 0 0 125 0 125 70.3 25:00.0 0 0 125 0 125 70.3 25:15.0 0 0 125 0 125 70.2 25:30.0 0 0 125 0 125 70.2 25:45.0 0 0 125 0 125 70.2 26:00.0 0 0 125 0 125 70.2 26:15.0 0 0 125 0 125 70.2 26:30.0 0 0 125 0 125 70.2 26:45.0 0 0 125 0 125 70.2 27:00.0 0 0 125 0 125 70.2 27:15.0 0 0 125 0 125 70.3 27:30.0 0 0 125 0 125 70.2 27:45.0 15.2 0 19 0 19 70.3 28:00.0 20.7 0 7 0 7 70.3 28:15.0 21 0 5 0 5 70.3 28:30.0 21 0 4 0 4 70.2 28:45.0 21 0 3 0 3 70.2 29:00.0 21 0 3 0 3 70.2 29:15.0 21 0 2 0 2 70.2 29:30.0 21 0 2 0 2 70.2 29:45.0 21 0 2 0 2 70.2
0 125 0 125 70.2 test phase

average 0.0 San Antonio, Texas Energy Developments August 26, 2009

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 30:00.0 21 0 2 0 2 70.2 30:15.0 10.6 0 78 0 78 70.2 30:30.0 0.2 0 120 0 120 70.2 30:45.0 0 0 122 0 122 70.2 31:00.0 0 0 124 0 124 70.2 31:15.0 0 0 124 0 124 70.2 31:30.0 0 0 124 0 124 70.2 31:45.0 0 0 124 0 124 70.2 32:00.0 0 0 124 0 124 70.2 32:15.0 0 0 124 0 124 70.2 32:30.0 0 0 124 0 124 70.2 32:45.0 0 0 124 0 124 70.2 33:00.0 0 0 124 0 124 70.2 33:15.0 0 0 125 0 125 70.2 33:30.0 0 0 125 0 125 70.2 33:45.0 0 0 125 0 125 70.2 34:00.0 0 0 125 0 125 70.2 34:15.0 0 0 125 0 125 70.2 34:30.0 0 0 125 0 125 70.2 34:45.0 0 0 125 0 125 70.3 35:00.0 0 0 125 0 125 70.3 35:15.0 0 0 125 0 125 70.3 35:30.0 0 0 125 0 125 70.3 35:45.0 0 0 125 0 125 70.3 36:00.0 0 0 125 0 125 70.2 36:15.0 0 0 125 0 125 70.2 36:30.0 0 0 125 0 125 70.2 36:45.0 0 0 125 0 125 70.2 37:00.0 0 0 125 0 125 70.2 37:15.0 17.7 0 15 0 15 70.3 37:30.0 20.8 0 6 0 6 70.3 37:45.0 21 0 5 0 5 70.3 38:00.0 21 0 4 0 4 70.3 38:15.0 21 0 3 0 3 70.3 38:30.0 21 0 3 0 3 70.3 38:45.0 21 0 3 0 3 70.3 39:00.0 21 0 2 0 2 70.3 39:15.0 21 0 2 0 2 70.3 39:30.0 21 0 2 0 2 70.3 39:45.0 21 0 2 0 2 70.3
0 125 0 125 70.3 test phase

average 0.0 San Antonio, Texas Energy Developments August 26, 2009

ed-09-sanantonio.tx-ecom# 3 -gases NORepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 48

O 2 CO NO NO 2 Start time: 0:00:00 (%) (ppm) (ppm) (ppm) 6.9 0.0 11.5 12.5 65.4 2.5 0.5 0.0 6.3 25.0 65.4 2.5 1.3 0.0 5.5 25.3 65.4 2.5 0.0 0.0 3.5 45.8 65.4 2.5 0.0 0.0 4.0 48.5 65.4 2.5 0.0 0.0 6.0 49.0 0.0 0.0 7.0 49.0 0.0 0.0 6.0 49.0 0.0 0.0 6.0 49.0 65.4 2.5 0.0 0.0 6.0 49.0 0.0 0.0 6.0 49.0 0.0 0.0 6.0 49.0 0.0 0.0 6.0 49.0 65.4 2.5 0.0 0.0 6.1 49.0 0.0% 

### Yes 2.0% 

### Yes 0.0 0.0 6.0 49.0 65.4 2.5 14.3 0.0 2.8 21.5 65.4 2.5 21.0 0.0 1.0 1.3 65.3 2.5 21.0 0.0 0.3 1.0 65.2 2.5

Stop Time:

Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Run #:

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314

Date: 8/26/2009

t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Repeatability Test

RAMPUP PHASE Cell Temp Flow Rate

t 8

t 10 Maximum Deviation (±2.0% or ±1 ppm) Acceptable Test Data Phase 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:15

0:09:45 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 t 13

## REFRESH PHASE t 9

t 14 t 15 t 7 1

9121OCVNXH San Antonio, Texas

Span Difference (±5.0% or ±1 ppm)

Acceptable Calibration Error t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes Sample Flow Rate are within specifications (±10% or as verified)

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 48

O 2 CO NO NO 2 Start time: 0:10:00 (%) (ppm) (ppm) (ppm) 15.9 0.0 4.3 4.8 65.2 2.5 0.0 0.0 7.3 28.5 65.1 2.5 0.0 0.0 5.5 43.8 65.1 2.5 0.0 0.0 6.3 44.5 65.0 2.5 0.0 0.0 7.0 48.0 65.0 2.5 0.0 0.0 7.0 49.0 0.0 0.0 7.0 49.0 0.0 0.0 8.0 49.0 0.0 0.0 8.0 49.0 65.0 2.5 0.0 0.0 8.0 49.0 0.0 0.0 8.0 49.0 0.0 0.0 8.0 49.0 0.0 0.0 8.0 49.0 64.9 2.5 0.0 0.0 7.8 49.0 0.0% 

### Yes 2.0% 

### Yes 0.0 0.0 8.0 49.0 64.9 2.5 15.0 0.0 3.5 20.3 64.8 2.5 21.0 0.0 1.0 1.5 64.8 2.5 21.0 0.0 0.0 1.0 64.8 2.5

Stop Time: San Antonio, Texas
Run #: 2 San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

210-623-1314

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Acceptable Test Data Phase Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 Span Difference (±5.0% or ±1 ppm)

t 15 0:19:45 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 48

O 2 CO NO NO 2 Start time: 0:20:00 (%) (ppm) (ppm) (ppm) 9.9 0.0 11.8 17.0 64.7 2.5 0.0 0.0 7.0 45.8 64.7 2.5 0.0 0.0 7.5 47.5 64.8 2.5 0.0 0.0 8.0 48.8 64.8 2.5 0.0 0.0 8.8 49.0 64.7 2.5 0.0 0.0 9.0 49.0 0.0 0.0 9.0 49.0 0.0 0.0 9.0 49.0 0.0 0.0 9.0 49.0 64.7 2.5 0.0 0.0 9.0 49.0 0.0 0.0 9.0 49.0 0.0 0.0 9.0 49.0 0.0 0.0 10.0 49.0 64.7 2.5 0.0 0.0 9.1 49.0 0.0% 

### Yes 2.0% 

### Yes 0.0 0.0 9.3 49.0 64.7 2.5 10.2 0.0 5.8 29.3 64.6 2.5 21.0 0.0 1.0 2.3 64.6 2.5 21.0 0.0 0.3 1.0 64.6 2.5

Stop Time: 210-623-1314 San Antonio, Texas 78252 San Antonio, Texas
Run #: 3

Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Acceptable Test Data Phase Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 Span Difference (±5.0% or ±1 ppm)

t 15 0:29:45 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 48

O 2 CO NO NO 2 Start time: 0:30:00 (%) (ppm) (ppm) (ppm) 7.3 0.0 12.8 25.3 64.6 2.5 0.0 0.0 4.0 46.0 64.6 2.5 0.0 0.0 4.5 48.0 64.5 2.5 0.0 0.0 5.0 48.5 64.5 2.5 0.0 0.0 5.0 49.0 64.5 2.5 0.0 0.0 5.0 49.0 0.0 0.0 5.0 49.0 0.0 0.0 5.0 49.0 0.0 0.0 5.0 49.0 64.4 2.5 0.0 0.0 4.0 49.0 0.0 0.0 4.0 49.0 0.0 0.0 4.0 49.0 0.0 0.0 4.0 49.0 64.4 2.5 0.0 0.0 4.5 49.0 0.0% 

### Yes 2.0% 

### Yes 0.0 0.0 4.0 49.0 64.4 2.5 10.3 0.0 2.3 29.5 64.4 2.5 21.0 0.0 0.5 3.3 64.4 2.5 21.0 0.0 0.0 2.0 64.3 2.5

Stop Time: 210-623-1314 San Antonio, Texas 78252 San Antonio, Texas
Run #: 4

Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

Cell Temp Calibration Gas Information 

## Measurement Cycle Repeatability Test

Flow Rate Date: 8/26/2009 Analyzer Response

t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5

Acceptable Test Data Phase Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30

t 10 t 11 t 12 t 13 t 14 Span Difference (±5.0% or ±1 ppm)

t 15 0:39:45 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9



### Yes

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatClient: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:00.0 21 0 1 0 1 65.4 00:15.0 6.6 0 32 0 32 65.4 00:30.0 0.1 0 7 25 32 65.4 00:45.0 0 0 6 25 31 65.4 01:00.0 0 0 6 25 31 65.4 01:15.0 0 0 6 25 31 65.4 01:30.0 0 0 6 25 31 65.4 01:45.0 2 0 7 25 32 65.4 02:00.0 3.3 0 7 25 32 65.4 02:15.0 1.9 0 7 25 32 65.4 02:30.0 0 0 4 25 29 65.4 02:45.0 0 0 4 26 30 65.4 03:00.0 0 0 3 43 46 65.4 03:15.0 0 0 3 44 47 65.4 03:30.0 0 0 4 48 52 65.4 03:45.0 0 0 4 48 52 65.4 04:00.0 0 0 4 48 52 65.4 04:15.0 0 0 4 48 52 65.4 04:30.0 0 0 4 49 53 65.4 04:45.0 0 0 4 49 53 65.4 05:00.0 0 0 6 49 55 65.4 05:15.0 0 0 7 49 56 65.4 05:30.0 0 0 6 49 55 65.4 05:45.0 0 0 6 49 55 65.4 06:00.0 0 0 6 49 55 65.4 06:15.0 0 0 6 49 55 65.4 06:30.0 0 0 6 49 55 65.4 06:45.0 0 0 6 49 55 65.4 07:00.0 0 0 6 49 55 65.4 07:15.0 15.6 0 3 27 30 65.4 07:30.0 20.7 0 1 7 8 65.4 07:45.0 21 0 1 3 4 65.3 08:00.0 21 0 1 2 3 65.3 08:15.0 21 0 1 1 2 65.3 08:30.0 21 0 1 1 2 65.3 08:45.0 21 0 1 1 2 65.2 09:00.0 21 0 1 1 2 65.2 09:15.0 21 0 0 1 1 65.2 09:30.0 21 0 0 1 1 65.2 09:45.0 21 0 0 1 1 65.2 August 26, 2009 Energy Developments San Antonio, Texas

49 55 65.4 test phase

average 0.0 0 6

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:00.0 21 0 0 1 1 65.2 10:15.0 21 0 0 1 1 65.2 10:30.0 21 0 0 1 1 65.1 10:45.0 0.5 0 17 16 33 65.1 11:00.0 0 0 9 22 31 65.1 11:15.0 0 0 8 17 25 65.1 11:30.0 0 0 7 33 40 65.1 11:45.0 0 0 5 42 47 65.1 12:00.0 0 0 5 44 49 65.1 12:15.0 0 0 5 44 49 65.1 12:30.0 0 0 6 44 50 65 12:45.0 0 0 6 43 49 65 13:00.0 0 0 6 43 49 65 13:15.0 0 0 6 45 51 65 13:30.0 0 0 6 45 51 65 13:45.0 0 0 7 45 52 65 14:00.0 0 0 7 48 55 65 14:15.0 0 0 7 48 55 65 14:30.0 0 0 7 48 55 65 14:45.0 0 0 7 48 55 65 15:00.0 0 0 7 49 56 65 15:15.0 0 0 7 49 56 65 15:30.0 0 0 8 49 57 64.9 15:45.0 0 0 8 49 57 64.9 16:00.0 0 0 8 49 57 64.9 16:15.0 0 0 8 49 57 64.9 16:30.0 0 0 8 49 57 64.8 16:45.0 0 0 8 49 57 64.8 17:00.0 0 0 8 49 57 64.8 17:15.0 18.2 0 3 22 25 64.8 17:30.0 20.8 0 2 7 9 64.8 17:45.0 21 0 1 3 4 64.8 18:00.0 21 0 1 2 3 64.8 18:15.0 21 0 1 2 3 64.8 18:30.0 21 0 1 1 2 64.8 18:45.0 21 0 1 1 2 64.8 19:00.0 21 0 0 1 1 64.8 19:15.0 21 0 0 1 1 64.8 19:30.0 21 0 0 1 1 64.8 19:45.0 21 0 0 1 1 64.8 Energy Developments August 26, 2009 San Antonio, Texas

8 49 57 64.9 test phase

average 0.0 0

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 20:00.0 21 0 0 1 1 64.7 20:15.0 18.3 0 23 2 25 64.7 20:30.0 0.4 0 16 24 40 64.7 20:45.0 0 0 8 41 49 64.7 21:00.0 0 0 7 45 52 64.7 21:15.0 0 0 7 46 53 64.7 21:30.0 0 0 7 46 53 64.7 21:45.0 0 0 7 46 53 64.7 22:00.0 0 0 7 46 53 64.7 22:15.0 0 0 7 48 55 64.7 22:30.0 0 0 8 48 56 64.8 22:45.0 0 0 8 48 56 64.8 23:00.0 0 0 8 48 56 64.8 23:15.0 0 0 8 49 57 64.8 23:30.0 0 0 8 49 57 64.7 23:45.0 0 0 8 49 57 64.7 24:00.0 0 0 8 49 57 64.7 24:15.0 0 0 9 49 58 64.7 24:30.0 0 0 9 49 58 64.7 24:45.0 0 0 9 49 58 64.7 25:00.0 0 0 9 49 58 64.7 25:15.0 0 0 9 49 58 64.7 25:30.0 0 0 9 49 58 64.7 25:45.0 0 0 9 49 58 64.7 26:00.0 0 0 9 49 58 64.7 26:15.0 0 0 9 49 58 64.7 26:30.0 0 0 9 49 58 64.7 26:45.0 0 0 10 49 59 64.7 27:00.0 0 0 10 49 59 64.6 27:15.0 0 0 10 49 59 64.6 27:30.0 19.8 0 2 14 16 64.6 27:45.0 20.9 0 1 5 6 64.6 28:00.0 21 0 1 3 4 64.6 28:15.0 21 0 1 2 3 64.6 28:30.0 21 0 1 2 3 64.6 28:45.0 21 0 1 2 3 64.6 29:00.0 21 0 1 1 2 64.6 29:15.0 21 0 0 1 1 64.6 29:30.0 21 0 0 1 1 64.6 29:45.0 21 0 0 1 1 64.6 August 26, 2009 San Antonio, Texas Energy Developments

9 49 58 64.7 test phase

average 0.0 0

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 30:00.0 21 0 0 1 1 64.6 30:15.0 8 0 41 10 51 64.6 30:30.0 0.1 0 6 44 50 64.6 30:45.0 0 0 4 46 50 64.6 31:00.0 0 0 4 46 50 64.6 31:15.0 0 0 4 46 50 64.5 31:30.0 0 0 4 46 50 64.6 31:45.0 0 0 4 46 50 64.5 32:00.0 0 0 4 48 52 64.5 32:15.0 0 0 4 48 52 64.5 32:30.0 0 0 5 48 53 64.5 32:45.0 0 0 5 48 53 64.5 33:00.0 0 0 5 48 53 64.5 33:15.0 0 0 5 48 53 64.5 33:30.0 0 0 5 49 54 64.5 33:45.0 0 0 5 49 54 64.5 34:00.0 0 0 5 49 54 64.5 34:15.0 0 0 5 49 54 64.5 34:30.0 0 0 5 49 54 64.5 34:45.0 0 0 5 49 54 64.5 35:00.0 0 0 5 49 54 64.5 35:15.0 0 0 5 49 54 64.4 35:30.0 0 0 5 49 54 64.4 35:45.0 0 0 5 49 54 64.4 36:00.0 0 0 4 49 53 64.4 36:15.0 0 0 4 49 53 64.4 36:30.0 0 0 4 49 53 64.4 36:45.0 0 0 4 49 53 64.4 37:00.0 0 0 4 49 53 64.4 37:15.0 0 0 3 49 52 64.4 37:30.0 20.2 0 1 14 15 64.4 37:45.0 21 0 1 6 7 64.4 38:00.0 21 0 1 4 5 64.4 38:15.0 21 0 1 3 4 64.4 38:30.0 21 0 0 3 3 64.4 38:45.0 21 0 0 3 3 64.4 39:00.0 21 0 0 2 2 64.4 39:15.0 21 0 0 2 2 64.3 39:30.0 21 0 0 2 2 64.3 39:45.0 21 0 0 2 2 64.3 August 26, 2009 San Antonio, Texas Energy Developments

5 49 54 64.4 test phase

average 0.0 0

ed-09-sanantonio.tx-ecom# 3 -gases NO2RepeatLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 124

O 2 CO NO NO 2 Start time: 0:00:15 (%) (ppm) (ppm) (ppm) 21.0 0.0 0.0 0.0 73.7 2.5 21.0 0.0 0.0 0.0 73.7 2.5 9.5 0.0 72.5 0.3 73.7 2.5 0.1 0.0 110.3 1.0 73.7 2.5 0.0 0.0 121.3 1.0 73.7 2.5 0.0 0.0 125.0 1.0 0.0 0.0 126.0 1.0 0.0 0.0 126.0 1.0 0.0 0.0 126.0 1.0 73.7 2.5 0.0 0.0 124.0 1.0 0.0 0.0 124.0 1.0 0.0 0.0 125.0 1.0 0.0 0.0 124.0 1.0 73.7 2.5 0.0 0.0 125.0 1.0 0.8% 

### Yes 0.8% 

### Yes 0.0 0.0 124.3 1.0 73.7 2.5 15.0 0.0 36.8 0.3 73.7 2.5 21.0 0.0 2.5 0.0 73.7 2.5 21.0 0.0 2.0 0.0 73.7 2.5

Stop Time:

Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Run #:

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314

Date: 8/27/2009

t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Pre-Cal Test

RAMPUP PHASE Cell Temp Flow Rate

Sample Flow Rate are within specifications (±10% or as verified) 0:10:00 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45

t 15 1

9121OCVNXH San Antonio, Texas

t 7 t 8

t 10 Maximum Deviation (±2.0% or ±1 ppm) Acceptable Test Data Phase t 5:15

Span Difference (±5.0% or ±1 ppm)

Acceptable Calibration Error t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes t 13

## REFRESH PHASE t 9

t 14

ed-09-sanantonio.tx-ecom# 3 -gases PreCalLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 48

O 2 CO NO NO 2 Start time: 0:00:15 (%) (ppm) (ppm) (ppm) 6.8 3.0 2.5 30.8 88.8 2.5 0.0 2.0 4.0 50.3 88.6 2.5 0.0 1.5 3.0 48.3 88.5 2.5 0.0 1.0 3.0 49.3 88.2 2.5 0.0 1.0 3.0 50.0 88.0 2.5 0.0 0.0 3.0 49.0 0.0 0.0 3.0 48.0 0.0 1.0 3.0 48.0 0.0 0.0 3.0 48.0 88.1 2.5 0.0 0.0 3.0 48.0 0.0 0.0 3.0 48.0 0.0 0.0 3.0 48.0 0.0 0.0 3.0 48.0 88.7 2.5 0.0 0.1 3.0 48.1 1.8% 

### Yes 0.3% 

### Yes 0.0 0.0 3.0 48.0 88.7 2.5 19.7 0.0 2.3 6.0 89.0 2.5 21.0 0.0 2.0 1.0 89.7 2.5 21.0 0.5 2.0 1.0 89.6 2.5

Stop Time: San Antonio, Texas
Run #: 2 Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH 210-623-1314

Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Pre-Cal Test

Flow Rate Date: 8/27/2009 Analyzer Response



## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5



## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00
Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 t 11 t 12 t 13 t 14 t 15 0:10:00 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes

ed-09-sanantonio.tx-ecom# 3 -gases PreCalLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 897

O 2 CO NO NO 2 Start time: 0:00:15 (%) (ppm) (ppm) (ppm) 6.0 492.8 2.8 0.0 90.2 2.5 0.0 889.3 3.0 0.0 90.6 2.5 0.0 895.5 3.0 0.0 90.4 2.5 0.0 896.8 3.0 0.0 89.2 2.5 0.0 895.5 3.0 0.0 88.6 2.5 0.0 896.0 3.0 0.0 0.0 896.0 3.0 0.0 0.0 896.0 3.0 0.0 0.0 895.0 3.0 0.0 88.4 2.5 0.0 895.0 3.0 0.0 0.0 894.0 3.0 0.0 0.0 894.0 3.0 0.0 0.0 893.0 3.0 0.0 88.5 2.5 0.0 894.9 3.0 0.0 0.2% 

### Yes 0.2% 

### Yes 0.0 894.0 3.0 0.0 88.5 2.5 19.7 255.8 2.0 0.0 87.8 2.5 21.0 9.3 2.0 0.0 88.4 2.5 21.0 4.5 2.0 0.0 88.2 2.5

Stop Time: San Antonio, Texas
Run #: 3
210-623-1314 Address: 8611 Covel Road San Antonio, Texas 78252
Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information

Cell Temp Calibration Gas Information 

## Measurement Cycle Pre-Cal Test

Flow Rate Date: 8/27/2009 Analyzer Response



## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5



## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00
Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00)

Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase
Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 t 11 t 12 t 13 t 14 t 15 0:10:00 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) 

### Yes

ed-09-sanantonio.tx-ecom# 3 -gases PreCalClient: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:15.0 21 0 0 0 0 73.6 00:30.0 21 0 0 0 0 73.6 00:45.0 21 0 0 0 0 73.7 01:00.0 21 0 0 0 0 73.7 01:15.0 21 0 0 0 0 73.7 01:30.0 21 0 0 0 0 73.7 01:45.0 21 0 0 0 0 73.7 02:00.0 21 0 0 0 0 73.7 02:15.0 21 0 0 0 0 73.7 02:30.0 14.1 0 79 0 79 73.7 02:45.0 2.2 0 104 0 104 73.7 03:00.0 0.5 0 107 1 108 73.7 03:15.0 0.2 0 109 1 110 73.7 03:30.0 0.1 0 110 1 111 73.7 03:45.0 0.1 0 111 1 112 73.7 04:00.0 0 0 111 1 112 73.7 04:15.0 0 0 112 1 113 73.7 04:30.0 0 0 124 1 125 73.7 04:45.0 0 0 124 1 125 73.7 05:00.0 0 0 125 1 126 73.7 05:15.0 0 0 125 1 126 73.7 05:30.0 0 0 126 1 127 73.7 05:45.0 0 0 126 1 127 73.7 06:00.0 0 0 126 1 127 73.7 06:15.0 0 0 124 1 125 73.7 06:30.0 0 0 124 1 125 73.7 06:45.0 0 0 125 1 126 73.7 07:00.0 0 0 124 1 125 73.7 07:15.0 0 0 124 1 125 73.7 07:30.0 18.2 0 13 0 13 73.7 07:45.0 20.7 0 6 0 6 73.7 08:00.0 21 0 4 0 4 73.7 08:15.0 21 0 3 0 3 73.7 08:30.0 21 0 3 0 3 73.7 08:45.0 21 0 2 0 2 73.7 09:00.0 21 0 2 0 2 73.7 09:15.0 21 0 2 0 2 73.7 09:30.0 21 0 2 0 2 73.7 09:45.0 21 0 2 0 2 73.7 10:00.0 21 0 2 0 2 73.7 August 27, 2009 Energy Developments San Antonio, Texas

126 73.7 test phase

average 0.0 0 125 1

ed-09-sanantonio.tx-ecom# 3 -gases PreCalCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:15.0 21 4 2 0 2 88.7 00:30.0 5.8 3 2 30 32 88.7 00:45.0 0.4 3 3 45 48 88.8 01:00.0 0 2 3 48 51 89 01:15.0 0 2 4 49 53 89 01:30.0 0 2 4 50 54 88.5 01:45.0 0 2 4 51 55 88.4 02:00.0 0 2 4 51 55 88.5 02:15.0 0 2 3 48 51 88.5 02:30.0 0 2 3 48 51 88.5 02:45.0 0 1 3 48 51 88.4 03:00.0 0 1 3 49 52 88.4 03:15.0 0 1 3 49 52 88.3 03:30.0 0 1 3 49 52 88.2 03:45.0 0 1 3 49 52 88.1 04:00.0 0 1 3 50 53 88.1 04:15.0 0 1 3 50 53 88.1 04:30.0 0 1 3 50 53 88.1 04:45.0 0 1 3 50 53 87.9 05:00.0 0 1 3 50 53 87.9 05:15.0 0 0 3 49 53 87.7 05:30.0 0 0 3 48 54 87.7 05:45.0 0 1 3 48 51 88.3 06:00.0 0 0 3 48 51 88.7 06:15.0 0 0 3 48 51 88.8 06:30.0 0 0 3 48 51 88.8 06:45.0 0 0 3 48 51 88.8 07:00.0 0 0 3 48 51 88.5 07:15.0 16.1 0 3 17 20 88.3 07:30.0 20.5 0 2 4 6 89 07:45.0 21 0 2 2 4 89 08:00.0 21 0 2 1 3 89.5 08:15.0 21 0 2 1 3 89.7 08:30.0 21 0 2 1 3 89.9 08:45.0 21 0 2 1 3 89.9 09:00.0 21 0 2 1 3 89.4 09:15.0 21 0 2 1 3 89.2 09:30.0 21 0 2 1 3 89.4 09:45.0 21 1 2 1 3 89.8 10:00.0 21 1 2 1 3 89.9 Energy Developments August 27, 2009 San Antonio, Texas

test phase

average 0.0 0 3 48 52 88.4

ed-09-sanantonio.tx-ecom# 3 -gases PreCalCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:15.0 21 0 2 0 2 89.8 00:30.0 2.6 353 3 0 3 90.1 00:45.0 0.2 761 3 0 3 90.2 01:00.0 0 857 3 0 3 90.5 01:15.0 0 882 3 0 3 90.5 01:30.0 0 889 3 0 3 90.7 01:45.0 0 892 3 0 3 90.8 02:00.0 0 894 3 0 3 90.2 02:15.0 0 895 3 0 3 90.1 02:30.0 0 895 3 0 3 90.3 02:45.0 0 895 3 0 3 90.5 03:00.0 0 897 3 0 3 90.5 03:15.0 0 897 3 0 3 90.1 03:30.0 0 897 3 0 3 89.3 03:45.0 0 897 3 0 3 88.7 04:00.0 0 896 3 0 3 88.5 04:15.0 0 896 3 0 3 88.5 04:30.0 0 896 3 0 3 88.8 04:45.0 0 895 3 0 3 88.8 05:00.0 0 895 3 0 3 88.4 05:15.0 0 896 3 0 3 88.4 05:30.0 0 896 3 0 3 88.2 05:45.0 0 896 3 0 3 88.1 06:00.0 0 895 3 0 3 89 06:15.0 0 895 3 0 3 88.7 06:30.0 0 894 3 0 3 89 06:45.0 0 894 3 0 3 88.5 07:00.0 0 893 3 0 3 87.7 07:15.0 16.3 734 2 0 2 87.4 07:30.0 20.5 206 2 0 2 87.8 07:45.0 21 59 2 0 2 87.9 08:00.0 21 24 2 0 2 88.2 08:15.0 21 14 2 0 2 88.2 08:30.0 21 10 2 0 2 88.3 08:45.0 21 7 2 0 2 88.6 09:00.0 21 6 2 0 2 88.3 09:15.0 21 5 2 0 2 88.1 09:30.0 21 5 2 0 2 87.9 09:45.0 20.9 4 2 0 2 88.2 10:00.0 21 4 2 0 2 88.6 August 27, 2009 Energy Developments San Antonio, Texas

0.0 895 3 0 3 88.5 test phase

average

ed-09-sanantonio.tx-ecom# 3 -gases PreCalLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 48

O 2 CO NO NO 2 Start time: 0:00:01 (%) (ppm) (ppm) (ppm) 11.0 2.0 3.5 22.8 87.6 2.5 0.0 1.5 4.0 49.8 87.1 2.5 0.0 1.0 4.0 49.5 86.5 2.5 0.0 1.0 4.0 48.5 86.1 2.5 0.0 1.0 4.0 49.0 86.4 2.5 0.0 1.0 4.0 49.0 0.0 1.0 4.0 49.0 0.0 1.0 4.0 49.0 0.0 1.0 4.0 49.0 87.2 2.5 0.0 1.0 4.0 50.0 0.0 1.0 4.0 50.0 0.0 1.0 4.0 50.0 0.0 1.0 4.0 50.0 87.1 2.5 0.0 1.0 4.0 49.5 1.0% 

### Yes 3.0% 

### Yes 0.0 1.0 4.0 50.0 87.1 2.5 15.1 1.0 3.3 20.8 86.8 2.5 21.0 1.0 3.0 4.0 86.1 2.5 21.0 0.5 2.0 2.0 85.3 2.5

Stop Time:
Sample Flow Rate are within specifications (±10% or as verified) 1

9121OCVNXH San Antonio, Texas

Span Difference (±5.0% or ±1 ppm)

Acceptable Calibration Error t 7:00 Average Concentration (t5:15 - t7:00)



### Yes Yes 0:09:46 Cell Temperature (±10F for each run, not to exceed 20F for test day) and t 11 t 12 t 13

## REFRESH PHASE t 9

t 14 t 15 t 7 t 8

t 10 Maximum Deviation (±2.0% or ±1 ppm) Acceptable Test Data Phase 

## TEST DATA PHASE t 6:00 t 6:15 t 6:30 t 6:45 t 5:15 t 5:30 t 5:45

t 3 t 4 t 5 

## Measurement Cycle Post-Cal Test

RAMPUP PHASE Cell Temp Flow Rate Date: 8/27/2009

t 2 Calibration Gas Information San Antonio, Texas 78252 210-623-1314 Address: 8611 Covel Road

Analyzer Response

t 1 Calibration Gas Verification Information

ECOM-AC Analyzer make & model: Run #:

ed-09-sanantonio.tx-ecom# 3 -gases PostCalLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 897

O 2 CO NO NO 2 Start time: 0:10:01 (%) (ppm) (ppm) (ppm) 6.0 476.3 3.0 0.5 84.6 2.5 0.0 899.0 4.0 0.0 83.7 2.5 0.0 899.3 4.0 0.0 83.3 2.5 0.0 897.5 4.0 0.0 82.8 2.5 0.0 894.0 4.0 0.0 82.2 2.5 0.0 894.0 4.0 0.0 0.0 894.0 4.0 0.0 0.0 894.0 4.0 0.0 0.0 894.0 4.0 0.0 81.6 2.5 0.0 894.0 4.0 0.0 0.0 894.0 4.0 0.0 0.0 894.0 4.0 0.0 0.0 894.0 4.0 0.0 81.4 2.5 0.0 894.0 4.0 0.0 0.0% 

### Yes 0.3% 

### Yes 0.0 894.0 4.0 0.0 81.4 2.5 15.0 414.8 3.3 0.3 81.4 2.5 21.0 13.3 2.0 1.0 81.6 2.5 21.0 6.0 2.0 1.0 81.7 2.5

Stop Time: 

### Yes t 15 0:19:46 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 t 11 t 12 t 13 t 14 Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Cell Temp Calibration Gas Information 

## Measurement Cycle Post-Cal Test

Flow Rate Date: 8/27/2009 Analyzer Response Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road

210-623-1314 San Antonio, Texas 78252 San Antonio, Texas
Run #: 2

ed-09-sanantonio.tx-ecom# 3 -gases PostCalLocation:

Phone: Serial #:
Gas type O 2 % CO ppm NO ppm NO 2 ppm Concentration 124

O 2 CO NO NO 2 Start time: 0:20:01 (%) (ppm) (ppm) (ppm) 11.0 2.3 63.0 1.0 81.6 2.5 0.0 0.0 124.3 1.8 81.4 2.5 0.0 0.0 126.5 1.0 81.5 2.5 0.0 0.0 127.8 1.0 82.7 2.5 0.0 0.0 124.3 1.0 82.7 2.5 0.0 0.0 125.0 1.0 0.0 0.0 125.0 1.0 0.0 0.0 125.0 1.0 0.0 0.0 125.0 1.0 82.5 2.5 0.0 0.0 125.0 1.0 0.0 0.0 125.0 1.0 0.0 0.0 125.0 0.0 0.0 0.0 125.0 0.0 82.9 2.5 0.0 0.0 125.0 0.8 0.0% 

### Yes 0.8% 

### Yes 0.0 0.0 125.0 0.5 82.9 2.5 15.1 0.8 38.5 0.5 83.1 2.5 21.0 2.0 6.0 1.0 83.2 2.5 21.0 2.0 4.5 1.0 83.8 2.5

Stop Time: 

### Yes t 15 0:29:46 Cell Temperature (±10F for each run, not to exceed 20F for test day) and 

### Yes Sample Flow Rate are within specifications (±10% or as verified) Acceptable Calibration Error



## REFRESH PHASE t 7 t 8 t 9 t 10 t 11 t 12 t 13 t 14 Span Difference (±5.0% or ±1 ppm)

Acceptable Test Data Phase Maximum Deviation (±2.0% or ±1 ppm) Average Concentration (t5:15 - t7:00) 

## TEST DATA PHASE t 5:15 t 5:30 t 5:45 t 6:00 t 6:15 t 6:30 t 6:45 t 7:00

## RAMPUP PHASE t 1 t 2 t 3 t 4 t 5 Cell Temp Calibration Gas Information 

## Measurement Cycle Post-Cal Test

Flow Rate Date: 8/27/2009 Analyzer Response Analyzer make & model: ECOM-AC 9121OCVNXH Calibration Gas Verification Information Address: 8611 Covel Road San Antonio, Texas 78252 San Antonio, Texas
Run #: 3
210-623-1314

ed-09-sanantonio.tx-ecom# 3 -gases PostCalClient: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 00:01.0 21 2 3 2 5 87.6 00:16.0 21 2 3 1 4 87.6 00:31.0 1.8 2 4 40 44 87.6 00:46.0 0.1 2 4 48 52 87.5 01:02.0 0 2 4 49 53 87.3 01:16.0 0 2 4 50 54 87.2 01:31.0 0 1 4 50 54 87 01:46.0 0 1 4 50 54 86.9 02:01.0 0 1 4 51 55 86.8 02:16.0 0 1 4 51 55 86.4 02:31.0 0 1 4 48 52 86.5 02:46.0 0 1 4 48 52 86.3 03:01.0 0 1 4 48 52 86.3 03:16.0 0 1 4 48 52 86.2 03:32.0 0 1 4 49 53 86.1 03:46.0 0 1 4 49 53 85.9 04:02.0 0 1 4 49 53 86 04:16.0 0 1 4 49 53 86.5 04:31.0 0 1 4 49 53 86.6 04:46.0 0 1 4 49 53 86.6 05:01.0 0 1 4 49 53 87.1 05:16.0 0 1 4 49 53 87.2 05:32.0 0 1 4 49 53 87.2 05:46.0 0 1 4 49 53 87.3 06:01.0 0 1 4 50 54 87.3 06:16.0 0 1 4 50 54 87 06:31.0 0 1 4 50 54 87 06:46.0 0 1 4 50 54 87.1 07:01.0 0 1 4 50 54 87.1 07:17.0 18.6 1 3 15 18 86.7 07:32.0 20.9 1 3 10 13 86.7 07:46.0 21 1 3 8 11 86.5 08:01.0 21 1 3 6 9 86.4 08:17.0 21 1 3 4 7 86.2 08:31.0 21 1 3 3 6 86 08:46.0 21 1 3 3 6 85.8 09:01.0 21 1 2 2 4 85.5 09:17.0 21 1 2 2 4 85.2 09:31.0 21 0 2 2 4 85.2 09:46.0 21 0 2 2 4 85.1
54 87.2 test phase

average 0.0 1 4 50 August 27, 2009 Energy Developments San Antonio, Texas

ed-09-sanantonio.tx-ecom# 3 -gases PostCalCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 10:01.0 21 0 2 1 3 84.9 10:17.0 2.5 280 3 1 4 84.7 10:32.0 0.2 758 3 0 3 84.5 10:46.0 0.1 867 4 0 4 84.4 11:01.0 0 895 4 0 4 84.1 11:17.0 0 904 4 0 4 83.8 11:31.0 0 899 4 0 4 83.6 11:46.0 0 898 4 0 4 83.4 12:01.0 0 899 4 0 4 83.3 12:16.0 0 899 4 0 4 83.3 12:32.0 0 900 4 0 4 83.3 12:46.0 0 899 4 0 4 83.1 13:01.0 0 899 4 0 4 82.9 13:16.0 0 898 4 0 4 82.8 13:31.0 0 897 4 0 4 82.7 13:47.0 0 896 4 0 4 82.6 14:01.0 0 894 4 0 4 82.3 14:16.0 0 894 4 0 4 82.2 14:32.0 0 894 4 0 4 82.1 14:46.0 0 894 4 0 4 82 15:01.0 0 894 4 0 4 81.9 15:16.0 0 894 4 0 4 81.5 15:31.0 0 894 4 0 4 81.5 15:46.0 0 894 4 0 4 81.5 16:02.0 0 894 4 0 4 81.6 16:16.0 0 894 4 0 4 81.4 16:31.0 0 894 4 0 4 81.4 16:47.0 0 894 4 0 4 81.3 17:01.0 0 867 4 0 4 81.2 17:16.0 18.2 594 4 0 4 81.3 17:31.0 20.8 150 3 0 3 81.4 17:47.0 21 48 2 1 3 81.5 18:01.0 21 22 2 1 3 81.5 18:16.0 21 13 2 1 3 81.5 18:32.0 21 10 2 1 3 81.6 18:46.0 21 8 2 1 3 81.6 19:01.0 21 7 2 1 3 81.7 19:17.0 21 6 2 1 3 81.7 19:31.0 21 6 2 1 3 81.6 19:46.0 21 5 2 1 3 81.6
4 0 4 81.5 test phase

average 0.0 894 San Antonio, Texas Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases PostCalCompany: Date: Location: Unit: Sample Time O2 CO NO NO2 NOx Tamb 0.013900463 21 5 2 0 2 81.5 0.014074074 21 4 11 0 11 81.5 0.014247685 1.6 0 114 2 116 81.6 0.014421296 0.2 0 125 2 127 81.6 0.014594907 0 0 124 2 126 81.5 0.014780093 0 0 124 2 126 81.5 0.014953704 0 0 124 2 126 81.4 0.015115741 0 0 125 1 126 81.2 0.015289352 0 0 126 1 127 81.3 0.015462963 0 0 126 1 127 81.5 0.015636574 0 0 127 1 128 81.5 0.015810185 0 0 127 1 128 81.8 0.015983796 0 0 127 1 128 82.3 0.016168981 0 0 128 1 129 82.6 0.016342593 0 0 128 1 129 82.9 0.01650463 0 0 128 1 129 82.8 0.016678241 0 0 124 1 125 82.8 0.016851852 0 0 124 1 125 82.7 0.017025463 0 0 124 1 125 82.7 0.017199074 0 0 125 1 126 82.7 0.017384259 0 0 125 1 126 82.5 0.017546296 0 0 125 1 126 82.5 0.017719907 0 0 125 1 126 82.5 0.017893519 0 0 125 1 126 82.5 0.01806713 0 0 125 1 126 82.9 0.018252315 0 0 125 1 126 82.9 0.018414352 0 0 125 0 125 82.9 0.018587963 0 0 125 0 125 82.9 0.018761574 0 0 125 0 125 83 0.018935185 18.6 1 13 0 13 83.1 0.019108796 20.8 1 9 1 10 83.1 0.019282407 21 1 7 1 8 83.1 0.019467593 21 2 7 1 8 83.1 0.01962963 21 2 6 1 7 83.1 0.019803241 21 2 6 1 7 83.2 0.019976852 21 2 5 1 6 83.2 0.020162037 21 2 5 1 6 83.4 0.020335648 21 2 5 1 6 83.7 0.020509259 21 2 4 1 5 83.8 0.020671296 21 2 4 1 5 84.1
125 1 126 82.7 test phase

average 0.0 0 San Antonio, Texas Energy Developments August 27, 2009

ed-09-sanantonio.tx-ecom# 3 -gases PostCal

# APPENDIX E FUEL ANALYSIS RECORDS

### Client: Energy Developments Location: San Antonio, Texas Date: Project #: ed-09-sanantonio.tx-ecom#2 Natural Gas - Fuel Analysis
Mole (%) Molecular 1 Weight (lb/lb-mole) Lbs Component per Lb-Mole

of Gas Wt. % of Component Ideal Gross 1,3 Heating Value (Btu/ft 3 ) Fuel Heat Value [HHV]

(Btu/SCF) Ideal Net 1,3 Heating Value (Btu/ft 3 ) Fuel Heat Value [LHV] (Btu/SCF)
Methane CH 4 47.700 16.0430 7.65 27.09 994.85 474.54 895.75 427.27 Ethane C 2 H 6 0.000 30.0700 0.00 0.00 1, 743.15 0.00 1,594.41 0.00 Propane C 3 H 8 0.000 44.0970 0.00 0.00 2, 478.35 0.00 2,280.17 0.00 iso-Butane iC 4 H 10 0.000 58.1230 0.00 0.00 3, 203.11 0.00 2,955.38 0.00 n-Butane nC 4 H 10 0.000 58.1230 0.00 0.00 3, 213.35 0.00 2,965.62 0.00 Iso-Pentane iC 5 H 12 0.000 72.1500 0.00 0.00 3, 940.87 0.00 3,643.50 0.00 n-Pentane nC 5 H 12 0.000 72.1500 0.00 0.00 3, 948.75 0.00 3,648.32 0.00 Hexanes C 6 H 14 0.000 86.1770 0.00 0.00 4, 684.54 0.00 4,337.82 0.00 Heptanes C 7 H 16 0.000 100.2040 0.00 0.00 5, 419.94 0.00 5,023.77 0.00 Octanes C 8 H 18 0.000 114.2310 0.00 0.00 6, 155.14 0.00 5,709.23 0.00 Carbon Dioxide CO 2 36.900 44.0100 16.24 57.49 0.00 0.00 0.00 0.00 Nitrogen N 2 12.800 28.0134 3.59 12.69 0.00 0.00 0.00 0.00 Hydrogen Sulfide H 2 S 0.000 34.0800 0.00 0.00 627.54 0.00 578.00 0.00 Oxygen O 2 2.400 31.9988 0.77 2.72 0.00 0.00 0.00 0.00 Helium He 0.000 4.0026 0.00 0.00 0.00 0.00 0.00 0.00 Hydrogen H 2 0.000 2.0159 0.00 0.00 319.34 0.00 269.82 0.00 99.800 28.25 100.00 dry 474.54 dry 427.27 wet 2,5 463.60 wet 2,5 417.42 Component Wt% 

### August 27, 2009

Standardized to 68 deg F and 14.696 psia - EPA St andards

Characteristics of Fuel Gas Gas Component

Totals

Molecular Weight of gas = 28.246 lb/lb-mole carbon 35.97 Btu per lb. of gas 4 = 6,472.003 gross (HHV) oxygen 44.52 Btu per lb. of gas 4 = 5,827.366 net (LHV) hydrogen 6.81 Density of fuel gas 2 = 0.0733 lb/cu. ft nitrogen 12.69 Wt % VOC in fuel gas = 0.00 % helium 0.00 Specific Gravity 1 = 0.9753 sulfur 0.00 Total 100.00 9,444.22

F-Factor Calculation: F-Factor = 1,000,000*((3.64*%H)+(1.53*%C)+(0.57*%S)+(0.14*%N )-(0.46*%O))/GCV GCV = Gross Btu per lb. of gas (HHV) %H, %C, %S, %N, & %O are percent weight values calculated from fuel analysis and have units of (scf/lb)/% Density of natural gas based on specific gravity multiplied by density of air at 68 deg F and 14.696 psia. Density of fuel oil based on lab analysis or specific gravity multiplied by density of water at 68 deg F and 14.696 psia.
References: 1 ASTM D 3588 2 Civil Engineering Reference Manual, 7th ed. - Michael R. Lindeburg 3 Mark's Standard Handbook for Mechanical Engineers, 10th ed. - Eugene A. Avallone, Theodore Baumeister III 4 Introduction to Fluid Mechanics, 3rd ed. - W illiam S. J anna 5 GPA Reference Bulletin 181-86, revised 1986, reprinted 1995 F-Factor (SCF dry exhaust per MMBtu [HHV]) = (Based on EPA RM-19) at 68 deg F and 14.696 psia

ed-09-sanantonio.tx-ecom# 3 -gases App. E