Name: Shawn Glacken

Title: Senior VP, Environmental Services

Company: Luminant

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Luminant Sandow 5A

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, January 20, 2011 Page 1 of 25
Luminant Sandow 5A

Facility Information:

Sandow 5 Generating Plant

3708 Charles Martin Hall Rd.

Rockdale TX 76567

Contact: Craig Birkenfeld

Phone: 214-875-8326

Fax: 214-875-8333

Email: craigbirkenfeld@luminant.com

Testing Company:

METCO Environmental

3226 Commander Blvd.

Carrollton TX 75006

Contact: Ned Shappley

Phone: 972-931-7127

Fax: 972-931-8398

Email: nshappley@metcoenv.com

Air Permit Number:

48437

Permitted Source ID/Name:

TX EPN SA-S5A

Permitted Maximum Process Rate:

2960 MMBtu/hr

Max. Normal Operation Process Rate:

New unit. No previous year ope

Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Circulating fluidized bed (CFB) boiler with limestone injection for primary sulfur control, burning lignite coal. 

SNCR with aqueous ammonia for NOx control, followed by Activated Carbon Injection for mercury control, then dry 

Scrubber for SO2 control, then Baghouse for PM control.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4833100012 FRS #: 110035206130

SCC / Description 10100318 External Combustion Boilers - Electric Generation - Lignite - Atmospheric 

Fluidized Bed Combustion - Circulating Bed 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack 192 0 0 0 122.833 128 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Carbon Monoxide Method 10 3 2 0

Total organic compounds 

(TOC) as Propane

Stack Method 25A 3 2 0

Stack Hydrogen Fluoride Method 26A 3 3 0

Stack Hydrogen Chloride Method 26A 3 3 0

Stack Filterable PM2.5 OTM - 27/28 3 4 0

Organic Condensible 

Particulate

Stack OTM - 27/28 3 4 0

Thursday, January 20, 2011 Page 2 of 25
Luminant Sandow 5A

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Method 26A was modified to collect HCN with the HCL and HF.The concentration of the sodium hydroxide solution 

used was increased from 0.1 N to 1 N (or higher), an additional impinger containing sodium hydroxide was added to 

the train (three impingers instead of two), the pH of the impinger solutions was

monitored periodically throughout the sample run. This modification was addressed on the Utility ICR website in the 

Frequently Asked Questions area (Question Test-025).

Stack Filterable Particulate OTM - 27/28 3 4 0

Inorganic (Aqueous) 

Condensible Part.

Stack OTM - 27/28 3 4 0

Stack Total Particulate OTM - 27/28 3 4 0

Stack Total PM2.5 OTM - 27/28 3 4 0

Stack Beryllium Method 29 3 4 0

Stack Manganese Method 29 3 4 0

Stack Chromium Method 29 3 4 0

Stack Cobalt Method 29 3 4 0

Stack Arsenic Method 29 3 4 0

Stack Filterable Particulate Method 29 3 4 0

Stack Antimony Method 29 3 4 0

Stack Lead Method 29 3 4 0

Stack Nickel Method 29 3 4 0

Stack Selenium Method 29 3 4 0

Stack Cadmium Method 29 3 4 0

Stack Co2 Method 3A CO2 6 0

Stack O2 Method 3A O2 6 0

Stack Sulfur Dioxide Method 6C 3 3 0

Stack Nitrogen oxides (NOx) Method 7E 3 3 0

Thursday, January 20, 2011 Page 3 of 25
Luminant Sandow 5A

Sampling / Stack Data Results Summary

Location Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 20, 2011 Page 4 of 25
Luminant Sandow 5A

Location Stack - Method 26A

Average

Run Number 1 2 3

Test Date 3/3/2010 3/4/2010 3/5/2010

Run Start Time 3:07:00 PM 2:40:00 PM 2:03:00 PM

Run Finish Time 6:18:00 PM 5:48:00 PM 5:11:00 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 103.836 97.680 102.599 101.372

Moisture Content of Stack Gas, % 19.36 19.03 17.52 18.637

Moisture Saturation at Stack Gas Temperature, % 66.50 65.29 67.30 66.363

Carbon Dioxide, % 16 15.8 16 15.933

Oxygen, % 3.7 3.8 3.7 3.733

Average Stack Gas Temperature, °F 191.64 190.81 192.31 191.587

Dry Volumetric Flow Rate, dry scfm 579,511.8 565,777.3 580,921.5 575,403.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 897,420.1 870,879.9 878,359.5 882,219.833

Percent Isokinetic of Sampling Rate, % 101.7 97.9 100.2 99.933

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Fw 11950 11950 11950 11,950.000

Fc 1910 1910 1910 1,910.000

Location Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, January 20, 2011 Page 5 of 25
Luminant Sandow 5A

Location Stack - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 20, 2011 Page 6 of 25
Luminant Sandow 5A

Location Stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 20, 2011 Page 7 of 25
Luminant Sandow 5A

Location Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, January 20, 2011 Page 8 of 25
Luminant Sandow 5A

Emissions Summary

Location: Stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

Elb/hr 8.09E+00 6.74E+00 6.68E+00 7.170

lb/mmBtuO2 2.78E-03 2.38E-03 2.29E-03 0.002

ppm 3.20E+00 2.73E+00 2.63E+00 2.853

ppm@7%O2 2.58E+00 2.21E+00 2.12E+00 2.303

Location: Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 1.03E+01 8.32E+00 1.61E+00 6.743

lb/mmBtuO2 3.54E-03 2.94E-03 5.51E-04 0.002

ppm 2.59E+00 2.14E+00 4.02E-01 1.711

ppm@7%O2 2.09E+00 1.74E+00 3.24E-01 1.385

Location: Stack - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.395 0.369 0.297 0.354

Elb/hr 2.92E-01 2.83E-01 2.22E-01 0.266

lb/mmBtuO2 1.00E-04 1.00E-04 7.65E-05 0.000

ppm 8.86E-02 8.80E-02 6.74E-02 0.081

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.404 0.378 0.305 0.362

Elb/hr 2.98E-01 2.90E-01 2.28E-01 0.272

lb/mmBtuO2 1.03E-04 1.03E-04 7.85E-05 0.000

ppm 1.65E-01 1.64E-01 1.26E-01 0.152

Location: Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0061 0.0113 0.0061 0.008

Elb/hr 3.32E-03 6.43E-03 3.39E-03 0.004

lb/mmBtuO2 1.14E-06 2.27E-06 1.14E-06 0.000

mg/dscm 1.54E-03 3.02E-03 1.52E-03 0.002

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.002 0.002 0.00135 0.002

Elb/hr 1.09E-03 1.14E-03 7.49E-04 0.001

lb/mmBtuO2 3.74E-07 4.02E-07 2.52E-07 0.000

Thursday, January 20, 2011 Page 9 of 25
Luminant Sandow 5A

mg/dscm 5.06E-04 5.35E-04 3.37E-04 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.001 0.001 0.001 0.001

Elb/hr 5.44E-04 5.69E-04 5.55E-04 0.001

lb/mmBtuO2 1.87E-07 2.01E-07 1.87E-07 0.000

mg/dscm 2.53E-04 2.67E-04 2.50E-04 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0011 0.00139 0.0025 0.002

Elb/hr 5.98E-04 7.91E-04 1.39E-03 0.001

lb/mmBtuO2 2.06E-07 2.79E-07 4.67E-07 0.000

mg/dscm 2.78E-04 3.72E-04 6.24E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0086 0.00129 0.00851 0.006

Elb/hr 4.68E-03 7.34E-04 4.72E-03 0.003

lb/mmBtuO2 1.61E-06 2.59E-07 1.59E-06 0.000

mg/dscm 2.18E-03 3.45E-04 2.13E-03 0.002

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.01 0.01 0.01 0.010

Elb/hr 5.44E-03 5.69E-03 5.55E-03 0.006

lb/mmBtuO2 1.87E-06 2.01E-06 1.87E-06 0.000

mg/dscm 2.53E-03 2.67E-03 2.50E-03 0.003

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 8.5 2.7 3.9 5.033

Elb/hr 4.62E+00 1.54E+00 2.16E+00 2.773

lb/mmBtuO2 1.59E-03 5.43E-04 7.28E-04 0.001

mg/dscm 2.15E+00 7.22E-01 9.74E-01 1.282

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00339 0.00211 0.00249 0.003

Elb/hr 1.84E-03 1.20E-03 1.38E-03 0.001

lb/mmBtuO2 6.34E-07 4.24E-07 4.65E-07 0.000

mg/dscm 8.58E-04 5.64E-04 6.22E-04 0.001

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.00209 0.00088 0.00107 0.001

Thursday, January 20, 2011 Page 10 of 25
Luminant Sandow 5A

Elb/hr 1.14E-03 5.01E-04 5.94E-04 0.001

lb/mmBtuO2 3.91E-07 1.77E-07 2.00E-07 0.000

mg/dscm 5.29E-04 2.35E-04 2.67E-04 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.003 0.00299 0.00383 0.003

Elb/hr 1.63E-03 1.70E-03 2.13E-03 0.002

lb/mmBtuO2 5.61E-07 6.01E-07 7.15E-07 0.000

mg/dscm 7.59E-04 7.99E-04 9.57E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.004 0.00321 0.00055 0.003

Elb/hr 2.18E-03 1.83E-03 3.05E-04 0.001

lb/mmBtuO2 7.48E-07 6.45E-07 1.03E-07 0.000

mg/dscm 1.01E-03 8.58E-04 1.37E-04 0.001

Location: Stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

Elb/hr 6.35E+01 2.61E+01 7.07E+00 32.223

lb/mmBtuO2 2.18E-02 9.23E-03 2.42E-03 0.011

ppm 1.10E+01 4.62E+00 1.22E+00 5.613

ppm@7%O2 8.87E+00 3.75E+00 9.85E-01 4.535

Location: Stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Elb/hr 2.29E+02 2.15E+02 2.25E+02 223.000

lb/mmBtuO2 7.87E-02 7.59E-02 7.69E-02 0.077

ppm 5.51E+01 5.29E+01 5.38E+01 53.933

ppm@7%O2 4.45E+01 4.29E+01 4.34E+01 43.600

Location: Stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 2.4 1.8 1.7 1.967

lb/mmBtuO2 5.07E-04 3.62E-04 3.11E-04 0.000

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 0.5 0.5 0.4 0.467

lb/mmBtuO2 1.06E-04 1.00E-04 7.32E-05 0.000

Thursday, January 20, 2011 Page 11 of 25
Luminant Sandow 5A

Process Run Data

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 79.4 69.9 172.4 107.233

lb/mmBtuO2 1.68E-02 1.40E-02 3.15E-02 0.021

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 1.5 45.3 1.4 16.067

lb/mmBtuO2 3.17E-04 9.10E-03 2.56E-04 0.003

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 82.4 116.1 174.6 124.367

lb/mmBtuO2 1.74E-02 2.33E-02 3.19E-02 0.024

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 80.5 114.8 173.3 122.867

lb/mmBtuO2 1.70E-02 2.31E-02 3.17E-02 0.024

Thursday, January 20, 2011 Page 12 of 25
Luminant Sandow 5A

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Lignite Burned 239 Tons/hr 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

65.3 lb/hr Brominated 

Carbon injection

0

1 Average Heat Input 2793 MMBtu/hr 0

1 Steam Output 2042 1000 lb steam/hr 0

1 Flue Gas Flow Rate 596010 DSCFM collected by 

METCO Env.

0

1 Flue Gas Oxygen Content 3.59 % collected by 

METCO Env.

0

1 Flue Gas Carbon Dioxide Content 16.09 % collected by 

METCO Env.

0

1 Flue Gas Moisture Content 18.62 % collected by 

METCO Env.

0

1 Flue Gas Sampling Point Temperature 191 Deg F collected by 

METCO Env.

0

1 Flue Gas Pressure 29.6 "Hg collected by 

METCO Env.

0

1 Standard Pressure 29.92 "Hg 0

1 Standard Temperature 68 Deg F 0

1 Unit Gross Electrical Output 641 Mwe 0

1 Unit Net Electric Generation 581 MW 0

2 Lignite Burned 232 Tons/hr 0

2 Sorbent Type and Sorbent Injection Rate (if 

applicable)

9.8 lb/hr Brominated 

Carbon injection

0

2 Average Heat Input 2824 MMBtu/hr 0

2 Steam Output 2045 1000 lb steam/hr 0

2 Flue Gas Flow Rate 611014 DSCFM collected by 

METCO Env.

0

2 Flue Gas Oxygen Content 3.76 % collected by 

METCO Env.

0

2 Flue Gas Carbon Dioxide Content 15.83 % collected by 

METCO Env.

0

2 Flue Gas Moisture Content 14.91 % collected by 

METCO Env.

0

2 Flue Gas Sampling Point Temperature 192 Deg F collected by 

METCO Env.

0

2 Flue Gas Pressure 29.61 "Hg collected by 

METCO Env.

0

2 Standard Pressure 29.92 "Hg 0

Thursday, January 20, 2011 Page 13 of 25
Luminant Sandow 5A

APCD Run Data

2 Standard Temperature 68 Deg F 0

2 Unit Gross Electrical Output 635 Mwe 0

2 Unit Net Electric Generation 576 MW 0

3 Lignite Burned 227 Tons/hr 0

3 Sorbent Type and Sorbent Injection Rate (if 

applicable)

9.8 lb/hr Brominated 

Carbon injection

0

3 Average Heat Input 2820 MMBtu/hr 0

3 Steam Output 2045 1000 lb steam/hr 0

3 Flue Gas Flow Rate 595801 DSCFM collected by 

METCO Env.

0

3 Flue Gas Oxygen Content 3.69 % collected by 

METCO Env.

0

3 Flue Gas Carbon Dioxide Content 16.06 % collected by 

METCO Env.

0

3 Flue Gas Moisture Content 17.78 % collected by 

METCO Env.

0

3 Flue Gas Sampling Point Temperature 192 Deg F collected by 

METCO Env.

0

3 Flue Gas Pressure 29.7 "Hg collected by 

METCO Env.

0

3 Standard Pressure 29.92 "Hg 0

3 Standard Temperature 68 Deg F 0

3 Unit Gross Electrical Output 622 Mwe 0

3 Unit Net Electric Generation 564 MW 0

Run Name Value UOM Comments

Target

Value

1 DRY LIMESTONE INJECTION 21.5 TPH 0

2 DRY LIMESTONE INJECTION 21.1 TPH 0

3 DRY LIMESTONE INJECTION 23.5 TPH 0

1 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

864 PPH 0

2 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

906 PPH 0

3 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

1083 PPH 0

1 ACTIVATED CARBON ADSORPTION 65.3 PPH 0

2 ACTIVATED CARBON ADSORPTION 65.3 PPH 0

3 ACTIVATED CARBON ADSORPTION 65.5 PPH 0

1 DRY SORBENT INJECTION 1299 PPH 0

Thursday, January 20, 2011 Page 14 of 25
Luminant Sandow 5A

Process Lab Run Data

2 DRY SORBENT INJECTION 1346 PPH 0

3 DRY SORBENT INJECTION 1307 PPH 0

1 DRY SCRUBBER 3.8 " H2O 0

2 DRY SCRUBBER 3.8 " H2O 0

3 DRY SCRUBBER 3.8 " H2O 0

1 BAGHOUSE 6.7 " H2O 0

2 BAGHOUSE 6.6 " H2O 0

3 BAGHOUSE 6.7 " H2O 0

Run Name Value UOM Comments

1 Fuel Heating Value 5632 Btu/lb

1 Fuel Moisture 30.16 %

1 Fuel Ash Content 25.23 %

1 Ultimate Analysis - Fuel Fixed Carbon 18.6 %

1 Ultimate Analysis - Fuel Carbon 32.2 %

1 Ultimate Analysis - Fuel Sulfur 1.12 %

1 Ultimate Analysis - Fuel Hydrogen 2.76 %

1 Ultimate Analysis - Fuel Nitrogen 0.64 %

1 Ultimate Analysis - Fuel Oxygen 7.89 %

1 Fuel Arsenic Content 2 ppm

1 Fuel Beryllium Content 1.8 ppm

1 Fuel Cadmium Content 0.5 ppm

1 Fuel Chromium Content 35 ppm

1 Fuel Cobalt Content 8 ppm

1 Fue Lead Content 19 ppm

1 Fuel Manganese Content 138 ppm

1 Fuel Nickel Content 20 ppm

1 Fuel Mercury Content 0.25 ppm

1 Fuel Selenium Content 8 ppm

1 Fuel Chlorine Content 43 ppm

1 Fuel Fluorine Content 13 ppm

1 Ultimate Analysis - Volatile Matter 26.01 %

1 Fuel Antimony Content 3 ppm

5 Fuel Heating Value 5785 Btu/lb

5 Fuel Moisture 29.78 %

5 Fuel Ash Content 24.72 %

5 Ultimate Analysis - Fuel Fixed Carbon 18.81 %

5 Ultimate Analysis - Fuel Carbon 32.65 %

5 Ultimate Analysis - Fuel Sulfur 1.41 %

5 Ultimate Analysis - Fuel Hydrogen 2.79 %

Thursday, January 20, 2011 Page 15 of 25
Luminant Sandow 5A

5 Ultimate Analysis - Fuel Nitrogen 0.65 %

5 Ultimate Analysis - Fuel Oxygen 8 %

5 Fuel Arsenic Content 2 ppm

5 Fuel Beryllium Content 1.8 ppm

5 Fuel Cadmium Content 0.5 ppm

5 Fuel Chromium Content 33 ppm

5 Fuel Cobalt Content 6 ppm

5 Fue Lead Content 16 ppm

5 Fuel Manganese Content 125 ppm

5 Fuel Nickel Content 20 ppm

5 Fuel Mercury Content 0.24 ppm

5 Fuel Selenium Content 8 ppm

5 Fuel Chlorine Content 76 ppm

5 Fuel Fluorine Content 130 ppm

5 Ultimate Analysis - Volatile Matter 26.69 %

5 Fuel Antimony Content 3 ppm

6 Fuel Heating Value 5903 Btu/lb

6 Fuel Moisture 30.52 %

6 Fuel Ash Content 23.09 %

6 Ultimate Analysis - Fuel Fixed Carbon 19.88 %

6 Ultimate Analysis - Fuel Carbon 33.63 %

6 Ultimate Analysis - Fuel Sulfur 1.19 %

6 Ultimate Analysis - Fuel Hydrogen 2.83 %

6 Ultimate Analysis - Fuel Nitrogen 0.66 %

6 Ultimate Analysis - Fuel Oxygen 8.08 %

6 Fuel Arsenic Content 4 ppm

6 Fuel Beryllium Content 1.7 ppm

6 Fuel Cadmium Content 0.5 ppm

6 Fuel Chromium Content 35 ppm

6 Fuel Cobalt Content 7 ppm

6 Fue Lead Content 17 ppm

6 Fuel Manganese Content 174 ppm

6 Fuel Nickel Content 25 ppm

6 Fuel Mercury Content 0.25 ppm

6 Fuel Selenium Content 9 ppm

6 Fuel Chlorine Content 60 ppm

6 Fuel Fluorine Content 120 ppm

6 Ultimate Analysis - Volatile Matter 26.51 %

6 Fuel Antimony Content 3 ppm

Thursday, January 20, 2011 Page 16 of 25
Luminant Sandow 5A

Sampling / Stack Data Results Detail

Location Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 20, 2011 Page 17 of 25
Luminant Sandow 5A

Location Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 20, 2011 Page 18 of 25
Luminant Sandow 5A

Location Stack - Method 26A

Average

Run Number 1 2 3

Test Date 3/3/2010 3/4/2010 3/5/2010

Run Start Time 3:07:00 PM 2:40:00 PM 2:03:00 PM

Run Finish Time 6:18:00 PM 5:48:00 PM 5:11:00 PM

Net Traversing Points 37 37 37

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.19 0.19 0.19 0.190

Pitot Tube Coefficient 0.801 0.801 0.801 0.801

Dry Gas Meter Calibration Factor 0.986 0.986 0.986 0.986

Barometric Pressure, inches of Mercury 29.68 29.71 29.76 29.717

Average Orifice Meter Differential, inches H2O 1.08 0.94 0.97 0.997

Dry Gas Meter Volume Sampled, cubic feet 107.627 100.999 105.620 104.749

Average Dry Gas Meter Temperature, °F 76.72 75.76 74.35 75.610

Dry Gas Meter Volume Sampled, dscf 103.836 97.680 102.599 101.372

Total Moisture Liquid collected, g 529.7 487.7 463.2 493.533

Volume of Water Vapor, standard cubic feet 24.93 22.96 21.80 23.230

Moisture Content of Stack Gas, % 19.36 19.03 17.52 18.637

Moisture Saturation at Stack Gas Temperature, % 66.50 65.29 67.30 66.363

Dry Mole Fraction 0.8064 0.8097 0.8248 0.814

Carbon Dioxide, % 16 15.8 16 15.933

Oxygen, % 3.7 3.8 3.7 3.733

Carbon Monoxide & Nitrogen, % 80.3 80.4 80.3 80.333

Fuel Factor 1.08 1.08 1.08

Dry Molecular Weight, lb/lb-Mole 30.71 30.68 30.71 30.700

Wet Molecular weight, lb/lb-Mole 28.25 28.27 28.48 28.333

Flue Gas Static Pressure, inches of H2O -1.5 -1.6 -1.6 -1.567

Absolute Flue Gas Pressure, inches of Mercury 29.57 29.59 29.64 29.600

Average Stack Gas Temperature, °F 191.64 190.81 192.31 191.587

Average Velocity Head, inches of H2O 1.5129352311

6944

1.428442393

75265

1.463145792

53842

1.468

Average Stack Gas Velocity, feet/second 74.39 72.19 72.81 73.130

Stack Cross-Sectional Area, square feet 201.062 201.062 201.062 201.062

Dry Volumetric Flow Rate, dry scfm 579,511.8 565,777.3 580,921.5 575,403.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 897,420.1 870,879.9 878,359.5 882,219.833

Percent Isokinetic of Sampling Rate, % 101.7 97.9 100.2 99.933

Percent Excess Air, % 21.1 21.8 21.1 21.333

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Round Duct Diameter, inches 192 192 192

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 11950 11950 11950 11,950.000

Fc 1910 1910 1910 1,910.000

Thursday, January 20, 2011 Page 19 of 25
Luminant Sandow 5A

Location Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, January 20, 2011 Page 20 of 25
Luminant Sandow 5A

Location Stack - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 20, 2011 Page 21 of 25
Luminant Sandow 5A

Location Stack - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 20, 2011 Page 22 of 25
Luminant Sandow 5A

Location Stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 20, 2011 Page 23 of 25
Luminant Sandow 5A

Location Stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 20, 2011 Page 24 of 25
Luminant Sandow 5A

Location Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, January 20, 2011 Page 25 of 25