### Name: Dan Giovanni

Title: Manager, Power Supply Operations an Company: Hawaiian Electric Company, Inc. Sign Date: 7/2/2010 Name: Tony Wong Title: President Company: AirKinetics Inc. Sign Date: 7/2/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## Emissions Testing Unit 6 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 10, 2011 Page 1 of 28

### Emissions Testing Unit 6

7/2/2010 Facility Information: HI, Waiau 475 Kamehameha Highway

Pearl City HI 96782 Contact: Stephen Ward
Phone: (808) 543-4535
Fax: (808) 543-4511
Email: stephen.ward@heco.com Testing Company:
AirKinetics Inc.
1308 S. Allec

Anaheim CA 92805 Contact: Tony Wong
Phone: (714) 245-1945
Fax: (714) 956-2350
Email: wongt@airkineticsinc.com

Air Permit Number: 0239-01-C Permitted Source ID/Name: 6
Permitted Maximum Process Rate: 637 MMBtu/hr Max. Normal Operation Process Rate: 562 MMBtu/hr Target Process Test Rate 538 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 1500300502 FRS #: 110000486420

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
stack 107.5 799 402 4 107.5 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 120 0 stack 2,3,7,8-TCDD Method 23 3 480 0 stack 1,2,3,7,8-PeCDD Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0 stack Regulation Description Compound Limit Unit



### Thursday, February 10, 2011 Page 2 of 28

### Emissions Testing Unit 6

7/2/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

None 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 stack OCDD Method 23 3 480 0 stack 2,3,7,8-TCDF Method 23 3 480 0 stack 1,2,3,7,8-PeCDF Method 23 3 480 0 stack 2,3,4,7,8-PeCDF Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0 stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0 stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 stack OCDF Method 23 3 480 0 stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0 stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 stack 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 stack

2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0 stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0 stack 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 stack

Total organic compounds

(TOC) as Propane Method 25A 3 120 0 stack

Hydrogen Fluoride Method 26 3 60 0 stack Hydrogen Chloride Method 26 3 60 0 stack Total PM2.5 OTM - 27/28 3 367 0 stack Beryllium Method 29 3 240 0 stack Arsenic Method 29 3 240 0 stack Cadmium Method 29 3 240 0 stack Chromium Method 29 3 240 0 stack Cobalt Method 29 3 240 0 stack Lead Method 29 3 240 0 stack Manganese Method 29 3 240 0 stack Nickel Method 29 3 240 0 stack Selenium Method 29 3 240 0 stack Antimony Method 29 3 240 0 stack O2 Method 3A O2 3 120 0 stack Co2 Method 3A CO2 3 120 0 stack Filterable Particulate Method 5 3 240 0 stack Sulfur Dioxide Method 6C 3 120 0 stack Nitrogen oxides (NOx) Method 7E 3 120 0 stack



### Thursday, February 10, 2011 Page 3 of 28

### Emissions Testing Unit 6

7/2/2010

Thursday, February 10, 2011 Page 4 of 28

### Emissions Testing Unit 6

7/2/2010 Sampling / Stack Data Results Summary



### Location stack - Method 10 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 10 3 Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 5 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 23 Average Run Number 1 2 3
Test Date 5/9/2010 5/10/2010 5/12/2010
Run Start Time 7:55:00 AM 7:36:00 AM 7:30:00 AM

Run Finish Time 4:17:00 PM 3:49:00 PM 3:53:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 336.443 354.449 368.879 353.257 Moisture Content of Stack Gas, % 11.18 10.77 10.82 10.923 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 12.8 12.2 11.9 12.300 Oxygen, % 4 4.5 5 4.500 Average Stack Gas Temperature, °F 294.79 299.54 310.88 301.737 Dry Volumetric Flow Rate, dry scfm 112,748.0 114,271.4 120,258.2 115,759.200 Actual Wet Volumetric Flue Gas Flow Rate, acfm 180,618.8 183,303.8 195,897.2 186,606.600 Percent Isokinetic of Sampling Rate, % 100.0 101.7 101.3 101.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Location stack - Method 25A Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 6 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 25A 3 Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 26 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 7 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 29 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location stack - Method 5 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 8 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 6C Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 7E Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 9 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - OTM - 27/28 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 10 of 28

### Emissions Testing Unit 6

7/2/2010 Emissions Summary



### Location: stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 5.98E-04 5.33E-04 5.77E-04 0.001 ppm 6.95E-01 6.19E-01 6.70E-01 0.661 ppm@7%O2 5.95E-01 5.30E-01 5.75E-01 0.567



### Location: stack - Method 10 3 Compound: Carbon Monoxide Average Run 4 5 6 lb/mmBtuO2 2.08E-04 3.27E-04 3.95E-04 0.000 ppm 2.38E-01 3.75E-01 4.54E-01 0.356 ppm@7%O2 2.07E-01 3.26E-01 3.94E-01 0.309



### Location: stack - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000236 0.0000000462 0.0000000114 0.000 lb/mmBtuO2 1.76E-12 3.37E-12 8.23E-13 0.000 ng/dscm 2.48E-03 4.60E-03 1.09E-03 0.003 ng/dscm@7%O2 2.04E-03 3.90E-03 9.53E-04 0.002


### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.00000000582 0.0000000275 0.0000000113 0.000 lb/mmBtuO2 4.33E-13 2.00E-12 8.16E-13 0.000 ng/dscm 6.11E-04 2.74E-03 1.08E-03 0.001 ng/dscm@7%O2 5.03E-04 2.32E-03 9.44E-04 0.001


### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.00000000702 0.00000000493 0.0000000065 0.000 lb/mmBtuO2 5.23E-13 3.59E-13 4.69E-13 0.000 ng/dscm 7.37E-04 4.91E-04 6.22E-04 0.001 ng/dscm@7%O2 6.06E-04 4.16E-04 5.44E-04 0.001


### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000155 0.0000000111 0.0000000137 0.000 lb/mmBtuO2 1.15E-12 8.09E-13 9.89E-13 0.000 ng/dscm 1.63E-03 1.11E-03 1.31E-03 0.001 ng/dscm@7%O2 1.34E-03 9.41E-04 1.15E-03 0.001



### Thursday, February 10, 2011 Page 11 of 28

### Emissions Testing Unit 6

7/2/2010 Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000854 0.0000000131 0.0000000119 0.000 lb/mmBtuO2 6.36E-13 9.54E-13 8.59E-13 0.000 ng/dscm 8.97E-04 1.31E-03 1.14E-03 0.001 ng/dscm@7%O2 7.38E-04 1.11E-03 9.97E-04 0.001


### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000145 0.0000000103 0.0000000128 0.000 lb/mmBtuO2 1.08E-12 7.50E-13 9.24E-13 0.000 ng/dscm 1.52E-03 1.03E-03 1.23E-03 0.001 ng/dscm@7%O2 1.25E-03 8.73E-04 1.08E-03 0.001


### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000803 0.0000000141 0.0000000111 0.000 lb/mmBtuO2 5.98E-13 1.03E-12 8.01E-13 0.000 ng/dscm 8.43E-04 1.41E-03 1.06E-03 0.001 ng/dscm@7%O2 6.93E-04 1.20E-03 9.27E-04 0.001


### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000141 0.0000000101 0.0000000125 0.000 lb/mmBtuO2 1.05E-12 7.36E-13 9.02E-13 0.000 ng/dscm 1.48E-03 1.01E-03 1.20E-03 0.001 ng/dscm@7%O2 1.22E-03 8.56E-04 1.05E-03 0.001


### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000102 0.00000000448 0.00000000514 0.000 lb/mmBtuO2 7.60E-13 3.26E-13 3.71E-13 0.000 ng/dscm 1.07E-03 4.46E-04 4.92E-04 0.001 ng/dscm@7%O2 8.80E-04 3.78E-04 4.30E-04 0.001


### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000083 0.0000000118 0.00000000669 0.000 lb/mmBtuO2 6.18E-13 8.60E-13 4.83E-13 0.000 ng/dscm 8.71E-04 1.18E-03 6.41E-04 0.001 ng/dscm@7%O2 7.16E-04 1.00E-03 5.60E-04 0.001


### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000103 0.0000000211 0.0000000195 0.000 lb/mmBtuO2 7.67E-13 1.54E-12 1.41E-12 0.000



### Thursday, February 10, 2011 Page 12 of 28

### Emissions Testing Unit 6

7/2/2010 ng/dscm 1.08E-03 2.10E-03 1.87E-03 0.002 ng/dscm@7%O2 8.88E-04 1.78E-03 1.63E-03 0.001


### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000357 0.0000462 0.0000519 0.000 lb/mmBtuO2 2.66E-09 3.37E-09 3.75E-09 0.000 ng/dscm 3.75E+00 4.60E+00 4.97E+00 4.440 ng/dscm@7%O2 3.08E+00 3.90E+00 4.34E+00 3.773


### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.001528 0.001743 0.002086 0.002 lb/mmBtuO2 1.14E-07 1.27E-07 1.51E-07 0.000 ng/dscm 1.60E+02 1.74E+02 2.00E+02 178.000 ng/dscm@7%O2 1.32E+02 1.47E+02 1.75E+02 151.333


### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.00605 0.00594 0.00715 0.006 lb/mmBtuO2 4.51E-07 4.33E-07 5.16E-07 0.000 ng/dscm 6.35E+02 5.92E+02 6.85E+02 637.333 ng/dscm@7%O2 5.22E+02 5.02E+02 5.99E+02 541.000


### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.000485 0.000524 0.0006 0.001 lb/mmBtuO2 3.61E-08 3.82E-08 4.33E-08 0.000 ng/dscm 5.09E+01 5.22E+01 5.74E+01 53.500 ng/dscm@7%O2 4.19E+01 4.42E+01 5.02E+01 45.433


### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.000342 0.000355 0.000388 0.000 lb/mmBtuO2 2.55E-08 2.59E-08 2.80E-08 0.000 ng/dscm 3.59E+01 3.54E+01 3.72E+01 36.167 ng/dscm@7%O2 2.95E+01 3.00E+01 3.25E+01 30.667


### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.0157 0.0148 0.0173 0.016 lb/mmBtuO2 1.17E-06 1.08E-06 1.25E-06 0.000 ng/dscm 1.65E+03 1.47E+03 1.66E+03 1,593.333 ng/dscm@7%O2 1.36E+03 1.25E+03 1.45E+03 1,353.333


### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3



### Thursday, February 10, 2011 Page 13 of 28

### Emissions Testing Unit 6

7/2/2010 Mass_mg 0.00019 0.000186 0.000217 0.000 lb/mmBtuO2 1.41E-08 1.35E-08 1.57E-08 0.000 ng/dscm 1.99E+01 1.85E+01 2.08E+01 19.733 ng/dscm@7%O2 1.64E+01 1.57E+01 1.82E+01 16.767


### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000087 0.0000000102 0.00000000437 0.000 lb/mmBtuO2 6.48E-13 7.43E-13 3.15E-13 0.000 ng/dscm 9.13E-04 1.02E-03 4.18E-04 0.001 ng/dscm@7%O2 7.51E-04 8.65E-04 3.65E-04 0.001


### Compound: 2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000097 0.0000000188 0.0000000232 0.000 lb/mmBtuO2 7.22E-13 1.37E-12 1.67E-12 0.000 ng/dscm 1.02E-03 1.87E-03 2.22E-03 0.002 ng/dscm@7%O2 8.39E-04 1.58E-03 1.94E-03 0.001


### Compound: 2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.00000000762 0.00000000924 0.00000000616 0.000 lb/mmBtuO2 5.67E-13 6.73E-13 4.45E-13 0.000 ng/dscm 8.00E-04 9.21E-04 5.90E-04 0.001 ng/dscm@7%O2 6.58E-04 7.81E-04 5.16E-04 0.001


### Compound: 2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.00000000999 0.0000000117 0.00000000909 0.000 lb/mmBtuO2 7.44E-13 8.52E-13 6.56E-13 0.000 ng/dscm 1.05E-03 1.17E-03 8.70E-04 0.001 ng/dscm@7%O2 8.64E-04 9.92E-04 7.61E-04 0.001


### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 7.45E-12 7.28E-12 7.22E-12 0.000 ng/dscm 1.05E-02 9.96E-03 9.57E-03 0.010 ng/dscm@7%O2 8.64E-03 8.44E-03 8.37E-03 0.008


### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.000074 0.0000677 0.0000962 0.000 lb/mmBtuO2 5.51E-09 4.93E-09 6.95E-09 0.000 ng/dscm 7.77E+00 6.75E+00 9.21E+00 7.910 ng/dscm@7%O2 6.39E+00 5.72E+00 8.05E+00 6.720



### Thursday, February 10, 2011 Page 14 of 28

### Emissions Testing Unit 6

7/2/2010 Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.000185 0.000144 0.000293 0.000 lb/mmBtuO2 1.38E-08 1.05E-08 2.12E-08 0.000 ng/dscm 1.94E+01 1.43E+01 2.81E+01 20.600 ng/dscm@7%O2 1.60E+01 1.21E+01 2.46E+01 17.567


### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.000263 0.000222 0.000256 0.000 lb/mmBtuO2 1.96E-08 1.62E-08 1.85E-08 0.000 ng/dscm 2.76E+01 2.21E+01 2.45E+01 24.733 ng/dscm@7%O2 2.27E+01 1.87E+01 2.14E+01 20.933


### Compound: OCDD Average RunNumber 1 2 3 Mass_mg 0.0000000423 0.0000000785 0.0000000354 0.000 lb/mmBtuO2 3.15E-12 5.72E-12 2.56E-12 0.000 ng/dscm 4.44E-03 7.82E-03 3.39E-03 0.005 ng/dscm@7%O2 3.65E-03 6.63E-03 2.96E-03 0.004


### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.0000000171 0.0000000146 0.000000012 0.000 lb/mmBtuO2 1.27E-12 1.06E-12 8.66E-13 0.000 ng/dscm 1.80E-03 1.45E-03 1.15E-03 0.001 ng/dscm@7%O2 1.48E-03 1.23E-03 1.01E-03 0.001



### Location: stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.72E-03 1.68E-03 1.39E-03 0.002 ppm 1.27E+00 1.24E+00 1.03E+00 1.180 ppm@7%O2 1.09E+00 1.06E+00 8.84E-01 1.011



### Location: stack - Method 25A 3 Compound: Total organic compounds (TOC) as Average Run 4 5 6 lb/mmBtuO2 1.84E-03 1.29E-03 1.41E-03 0.002 ppm 1.34E+00 9.42E-01 1.03E+00 1.104 ppm@7%O2 1.17E+00 8.18E-01 8.93E-01 0.960



### Location: stack - Method 26 Compound: Hydrogen Chloride Average RunNumber 1 2 3


### Thursday, February 10, 2011 Page 15 of 28

### Emissions Testing Unit 6

7/2/2010 Mass_mg 0.739 0.29 0.303 0.444 lb/mmBtuO2 5.55E-04 2.19E-04 2.26E-04 0.000


### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 0.216 0.216 0.21 0.214 lb/mmBtuO2 1.62E-04 1.63E-04 1.56E-04 0.000



### Location: stack - Method 29 

### Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.003081 0.00311 0.00346 0.003 lb/mmBtuO2 5.02E-07 4.55E-07 4.99E-07 0.000


### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.0181 0.01929 0.01794 0.018 lb/mmBtuO2 2.95E-06 2.82E-06 2.59E-06 0.000


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.00101 0.0011 0.00103 0.001 lb/mmBtuO2 1.65E-07 1.61E-07 1.48E-07 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.00093 0.00136 0.00085 0.001 lb/mmBtuO2 1.52E-07 1.99E-07 1.22E-07 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.00563 0.00634 0.0059 0.006 lb/mmBtuO2 9.18E-07 9.28E-07 8.50E-07 0.000


### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.117045 0.12203 0.121032 0.120 lb/mmBtuO2 1.91E-05 1.79E-05 1.74E-05 0.000


### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.0108 0.0089 0.0054 0.008 lb/mmBtuO2 1.76E-06 1.30E-06 7.78E-07 0.000



### Thursday, February 10, 2011 Page 16 of 28

### Emissions Testing Unit 6

7/2/2010

Process Run Data Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.0755 0.0828 0.07983 0.079 lb/mmBtuO2 1.23E-05 1.21E-05 1.15E-05 0.000


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 2.711 2.821 2.8511 2.794 lb/mmBtuO2 4.42E-04 4.13E-04 4.11E-04 0.000


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.008 0.0074 0.0064 0.007 lb/mmBtuO2 1.30E-06 1.08E-06 9.22E-07 0.000



### Location: stack - Method 5 Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 58.4 58.6 58.4 58.467 lb/mmBtuO2 9.52E-03 8.58E-03 8.42E-03 0.009



### Location: stack - Method 6C 

### Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 3.19E-01 3.16E-01 3.14E-01 0.316 ppm 1.62E+02 1.61E+02 1.59E+02 160.667 ppm@7%O2 1.39E+02 1.38E+02 1.37E+02 138.000



### Location: stack - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 1 2 3 lb/mmBtuO2 6.68E-01 6.80E-01 6.65E-01 0.671 ppm 4.73E+02 4.81E+02 4.70E+02 474.667 ppm@7%O2 4.05E+02 4.12E+02 4.04E+02 407.000



### Location: stack - OTM - 27/28 Compound: Total PM2.5 Average RunNumber 1 2 3 Mass_mg 82.7 85.3 80.1 82.700 lb/mmBtuO2 1.60E-02 1.71E-02 1.63E-02 0.016



### Thursday, February 10, 2011 Page 17 of 28

### Emissions Testing Unit 6

7/2/2010 Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 0


### 2 0
1 0
2 0


### 1 0
2 0
1 0


### 2 0
1 0
2 0


### 1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
1 0


### 1 Unit Gross Electric Generation 0 Mwe
1 Unit Net Electric Generation 0 MWh
1 Steam Output 0 1,000 lbs steam/hr


### 1 Average Heat Input 0 MMBtu/hr
1 Fuel Oil Firing Rate 0 Klb/hr

Run Name Value UOM Comments Target Value 

### 1 None 0
1 0
1 0


### 1 0

Run Name Value UOM Comments 1 none 0 1 0 

### 1 0 1 0 1 0



### Thursday, February 10, 2011 Page 18 of 28

### Emissions Testing Unit 6

7/2/2010 Sampling / Stack Data Results Detail



### Location stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 19 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 10 3 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 20 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 23 Average Run Number 1 2 3 Test Date 5/9/2010 5/10/2010 5/12/2010 Run Start Time 7:55:00 AM 7:36:00 AM 7:30:00 AM Run Finish Time 4:17:00 PM 3:49:00 PM 3:53:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.268 0.271 0.27 0.270 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.03 0.96 0.96 0.983 Barometric Pressure, inches of Mercury 30.1 30.1 30.1 30.100 Average Orifice Meter Differential, inches H2O 1.71 1.85 2.04 1.867 Dry Gas Meter Volume Sampled, cubic feet 337.284 380.727 398.952 372.321 Average Dry Gas Meter Temperature, °F 90.77 90.21 94.25 91.743 Dry Gas Meter Volume Sampled, dscf 336.443 354.449 368.879 353.257 Total Moisture Liquid collected, g 899.8 909.1 950.5 919.800 Volume of Water Vapor, standard cubic feet 42.35 42.79 44.74 43.293 Moisture Content of Stack Gas, % 11.18 10.77 10.82 10.923 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8882 0.8923 0.8918 0.891 Carbon Dioxide, % 12.8 12.2 11.9 12.300 Oxygen, % 4 4.5 5 4.500 Carbon Monoxide & Nitrogen, % 83.2 83.3 83.1 83.200 Fuel Factor 1.32 1.34 1.34 Dry Molecular Weight, lb/lb-Mole 30.21 30.13 30.10 30.147 Wet Molecular weight, lb/lb-Mole 28.84 28.82 28.79 28.817 Flue Gas Static Pressure, inches of H2O -0.48 -0.35 -0.35 -0.393 Absolute Flue Gas Pressure, inches of Mercury 30.06 30.07 30.07 30.067 Average Stack Gas Temperature, °F 294.79 299.54 310.88 301.737 Average Velocity Head, inches of H2O 0.5081004480 51847 0.519845625

049523 0.584273732

560152 0.537

Average Stack Gas Velocity, feet/second 47.76 48.47 51.80 49.343 Stack Cross-Sectional Area, square feet 63.030 63.030 63.030 63.030 Dry Volumetric Flow Rate, dry scfm 112,748.0 114,271.4 120,258.2 115,759.200 Actual Wet Volumetric Flue Gas Flow Rate, acfm 180,618.8 183,303.8 195,897.2 186,606.600 Percent Isokinetic of Sampling Rate, % 100.0 101.7 101.3 101.000 Percent Excess Air, % 22.3 25.7 29.5 25.833 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 107.5 107.5 107.5 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 21 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 22 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 25A 3 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 23 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 26 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 24 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 25 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 5 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 26 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 27 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 28 of 28

### Emissions Testing Unit 6

7/2/2010

Location stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 29 of 28