Name: Stephen Ward

Title: Senior Environmental Scientist

Company: Hawaiian Electric Company, Inc.

Sign Date:

Name: Tony Wong

Title: President

Company: AirKinetics Inc.

Sign Date: 8/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Emissions Testing Unit 9

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 10, 2011 Page 1 of 30
Emissions Testing Unit 9

Facility Information:

HI, Honolulu

170 Ala Moana Blv.

Honolulu HI 96813

Contact: Stephen Ward

Phone: (808) 543-4535

Fax: (808) 543-4511

Email: stephen.ward@heco.com

Testing Company:

AirKinetics Inc.

1308 S. Allec

Anaheim CA 92805

Contact:Tony Wong

Phone: (714) 245-1945

Fax: (714) 956-2350

Email: wongt@airkineticsinc.com

Air Permit Number:

0238-01-C

Permitted Source ID/Name:

9

Permitted Maximum Process Rate:

631.5 MMBtu/hr

Max. Normal Operation Process Rate:

605 MMBtu/hr

Target Process Test Rate

581 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process. “Please

 note that all information within this ERT has designated the boiler ID as Honolulu Unit 9. The Unit 9 designation is 

consistent with EPA’s designation through the Dept. of Heath and the state permit number. However, the ICR letter 

addresses the Honolulu boiler as "17" based on the EIA designation, instead of as "9". The 17 nomenclature is very 

old and cannot be changed. According to EIA guidelines, existing generator and boiler IDs cannot be changed in 

order to preserve continuity between the current reporting year data and historical data.”

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1500300500 FRS #: 110027161568

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 108 0 0 108 220 240 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Carbon Monoxide Method 10 3 120 0

stack 2,3,7,8-TCDD Method 23 3 480 0

stack 1,2,3,7,8-PeCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

Thursday, February 10, 2011 Page 2 of 30
Emissions Testing Unit 9

stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

stack OCDD Method 23 3 480 0

stack 2,3,7,8-TCDF Method 23 3 480 0

stack 1,2,3,7,8-PeCDF Method 23 3 480 0

stack 2,3,4,7,8-PeCDF Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

stack OCDF Method 23 3 480 0

stack Other TCDD Method 23 3 480 0

stack Other PeCDD Method 23 3 480 0

stack Other HxCDD Method 23 3 480 0

stack Other HpCDD Method 23 3 480 0

stack Other TCDF Method 23 3 480 0

stack Other PeCDF Method 23 3 480 0

stack Other HxCDF Method 23 3 480 0

stack Other HpCDF Method 23 3 480 0

stack Total Dioxins Method 23 3 480 0

stack Total Furans Method 23 3 480 0

stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

stack Method 23 3 480 0

stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

stack Method 23 3 480 0

stack Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

stack Method 25A 3 120 0

stack Hydrogen Chloride Method 26 3 60 0

stack Hydrogen Fluoride Method 26 3 60 0

stack Total Particulate OTM - 27/28 3 367 0

stack Filterable Particulate OTM - 27/28 3 367 0

Inorganic (Aqueous) 

Condensible Part.

stack OTM - 27/28 3 367 0

Organic Condensible 

Particulate

stack OTM - 27/28 3 367 0

stack Filterable PM2.5 OTM - 27/28 3 367 0

stack Total PM2.5 OTM - 27/28 3 367 0

stack Manganese Method 29 3 240 0

stack Antimony Method 29 3 240 0

Thursday, February 10, 2011 Page 3 of 30
Emissions Testing Unit 9

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

stack Arsenic Method 29 3 240 0

stack Beryllium Method 29 3 240 0

stack Cadmium Method 29 3 240 0

stack Chromium Method 29 3 240 0

stack Lead Method 29 3 240 0

stack Nickel Method 29 3 240 0

stack Selenium Method 29 3 240 0

stack Cobalt Method 29 3 240 0

stack O2 Method 3A O2 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack Filterable Particulate Method 5 0

stack Sulfur Dioxide Method 6C 3 120 0

stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, February 10, 2011 Page 4 of 30
Emissions Testing Unit 9

Sampling / Stack Data Results Summary

Location stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 23

Average

Run Number 1 2 3

Test Date 4/12/2010 4/14/2010 4/15/2010

Run Start Time 8:09:00 AM 7:40:00 

AM

7:20:00 AM

Run Finish Time 5:17:00 PM 4:18:00 PM 4:23:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 389.968 399.345 400.059 396.457

Moisture Content of Stack Gas, % 9.97 9.47 9.33 9.590

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.1 11 10.6 10.900

Oxygen, % 6.2 6.3 6.7 6.400

Average Stack Gas Temperature, °F 311.79 311.50 310.17 311.153

Dry Volumetric Flow Rate, dry scfm 143,951.8 144,734.7 146,075.0 144,920.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 233,563.5 233,448.9 234,059.7 233,690.700

Percent Isokinetic of Sampling Rate, % 98.1 99.9 99.2 99.067

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 5 of 30
Emissions Testing Unit 9

Location stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 6 of 30
Emissions Testing Unit 9

Location stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 7 of 30
Emissions Testing Unit 9

Location stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 10, 2011 Page 8 of 30
Emissions Testing Unit 9

Location stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 9 of 30
Emissions Testing Unit 9

Emissions Summary

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 3.18E-04 2.61E-04 8.99E-04 0.000

ppm 3.39E-01 2.79E-01 9.67E-01 0.528

ppm@7%O2 3.16E-01 2.60E-01 8.95E-01 0.490

Location: stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000684 0.0000000105 0.00000000869 0.000

lb/mmBtuO2 5.05E-13 7.63E-13 6.48E-13 0.000

ng/dscm 6.20E-04 9.29E-04 7.67E-04 0.001

ng/dscm@7%O2 5.86E-04 8.84E-04 7.51E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000047 0.00000000629 0.00000000719 0.000

lb/mmBtuO2 3.47E-13 4.57E-13 5.36E-13 0.000

ng/dscm 4.26E-04 5.56E-04 6.35E-04 0.001

ng/dscm@7%O2 4.03E-04 5.29E-04 6.22E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000555 0.00000000523 0.00000000667 0.000

lb/mmBtuO2 4.10E-13 3.80E-13 4.97E-13 0.000

ng/dscm 5.03E-04 4.63E-04 5.89E-04 0.001

ng/dscm@7%O2 4.76E-04 4.41E-04 5.77E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000787 0.0000000103 0.00000000882 0.000

lb/mmBtuO2 5.81E-13 7.48E-13 6.57E-13 0.000

ng/dscm 7.13E-04 9.11E-04 7.79E-04 0.001

ng/dscm@7%O2 6.74E-04 8.67E-04 7.63E-04 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000304 0.00000000241 0.00000000316 0.000

lb/mmBtuO2 2.25E-13 1.75E-13 2.36E-13 0.000

ng/dscm 2.75E-04 2.13E-04 2.79E-04 0.000

ng/dscm@7%O2 2.60E-04 2.03E-04 2.73E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

Thursday, February 10, 2011 Page 10 of 30
Emissions Testing Unit 9

RunNumber 1 2 3

Mass_mg 0.00000000733 0.0000000096 0.00000000822 0.000

lb/mmBtuO2 5.41E-13 6.97E-13 6.13E-13 0.000

ng/dscm 6.64E-04 8.49E-04 7.26E-04 0.001

ng/dscm@7%O2 6.28E-04 8.08E-04 7.11E-04 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000386 0.00000000422 0.00000000307 0.000

lb/mmBtuO2 2.85E-13 3.06E-13 2.29E-13 0.000

ng/dscm 3.50E-04 3.73E-04 2.71E-04 0.000

ng/dscm@7%O2 3.31E-04 3.55E-04 2.65E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000714 0.00000000935 0.00000000801 0.000

lb/mmBtuO2 5.27E-13 6.79E-13 5.97E-13 0.000

ng/dscm 6.47E-04 8.27E-04 7.07E-04 0.001

ng/dscm@7%O2 6.12E-04 7.87E-04 6.92E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000364 0.00000000289 0.00000000378 0.000

lb/mmBtuO2 2.69E-13 2.10E-13 2.82E-13 0.000

ng/dscm 3.30E-04 2.56E-04 3.34E-04 0.000

ng/dscm@7%O2 3.12E-04 2.44E-04 3.27E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000814 0.0000000054 0.00000000605 0.000

lb/mmBtuO2 6.01E-13 3.92E-13 4.51E-13 0.000

ng/dscm 7.37E-04 4.78E-04 5.34E-04 0.001

ng/dscm@7%O2 6.97E-04 4.55E-04 5.23E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000011 0.0000000109 0.00000000719 0.000

lb/mmBtuO2 8.13E-13 7.92E-13 5.36E-13 0.000

ng/dscm 9.96E-04 9.64E-04 6.35E-04 0.001

ng/dscm@7%O2 9.42E-04 9.18E-04 6.22E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.00000000687 0.000000144 0.0000000392 0.000

lb/mmBtuO2 5.07E-13 1.05E-11 2.92E-12 0.000

ng/dscm 6.22E-04 1.27E-02 3.46E-03 0.006

ng/dscm@7%O2 5.88E-04 1.21E-02 3.39E-03 0.005

Thursday, February 10, 2011 Page 11 of 30
Emissions Testing Unit 9

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000003403 0.000006026 0.000001897 0.000

lb/mmBtuO2 2.51E-11 4.38E-10 1.41E-10 0.000

ng/dscm 3.08E-02 5.33E-01 1.67E-01 0.244

ng/dscm@7%O2 2.91E-02 5.07E-01 1.63E-01 0.233

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000144 0.0000173 0.00000575 0.000

lb/mmBtuO2 1.06E-10 1.26E-09 4.29E-10 0.000

ng/dscm 1.30E-01 1.53E+00 5.08E-01 0.723

ng/dscm@7%O2 1.23E-01 1.46E+00 4.97E-01 0.693

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000114 0.00000182 0.000000535 0.000

lb/mmBtuO2 8.42E-12 1.32E-10 3.99E-11 0.000

ng/dscm 1.03E-02 1.61E-01 4.72E-02 0.073

ng/dscm@7%O2 9.74E-03 1.53E-01 4.62E-02 0.070

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000911 0.00000105 0.000000339 0.000

lb/mmBtuO2 6.73E-12 7.63E-11 2.53E-11 0.000

ng/dscm 8.25E-03 9.29E-02 2.99E-02 0.044

ng/dscm@7%O2 7.80E-03 8.84E-02 2.93E-02 0.042

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000384 0.000042 0.0000139 0.000

lb/mmBtuO2 2.84E-10 3.05E-09 1.04E-09 0.000

ng/dscm 3.48E-01 3.71E+00 1.23E+00 1.763

ng/dscm@7%O2 3.29E-01 3.53E+00 1.20E+00 1.686

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000599 0.000000531 0.000000185 0.000

lb/mmBtuO2 4.42E-12 3.86E-11 1.38E-11 0.000

ng/dscm 5.43E-03 4.70E-02 1.63E-02 0.023

ng/dscm@7%O2 5.13E-03 4.47E-02 1.60E-02 0.022

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000309 0.00000000246 0.00000000322 0.000

lb/mmBtuO2 2.28E-13 1.79E-13 2.40E-13 0.000

Thursday, February 10, 2011 Page 12 of 30
Emissions Testing Unit 9

ng/dscm 2.80E-04 2.18E-04 2.84E-04 0.000

ng/dscm@7%O2 2.65E-04 2.08E-04 2.78E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000114 0.0000000112 0.00000000742 0.000

lb/mmBtuO2 8.42E-13 8.13E-13 5.53E-13 0.000

ng/dscm 1.03E-03 9.91E-04 6.55E-04 0.001

ng/dscm@7%O2 9.74E-04 9.43E-04 6.41E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000572 0.00000000508 0.00000000488 0.000

lb/mmBtuO2 4.23E-13 3.69E-13 3.64E-13 0.000

ng/dscm 5.18E-04 4.49E-04 4.31E-04 0.000

ng/dscm@7%O2 4.90E-04 4.27E-04 4.22E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000857 0.00000000803 0.000000008 0.000

lb/mmBtuO2 6.33E-13 5.83E-13 5.96E-13 0.000

ng/dscm 7.76E-04 7.10E-04 7.06E-04 0.001

ng/dscm@7%O2 7.34E-04 6.76E-04 6.91E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000000205 0.00000000312 0.00000000267 0.000

lb/mmBtuO2 1.51E-13 2.27E-13 1.99E-13 0.000

ng/dscm 1.86E-04 2.76E-04 2.36E-04 0.000

ng/dscm@7%O2 1.76E-04 2.63E-04 2.31E-04 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000168 0.000000245 0.0000000707 0.000

lb/mmBtuO2 1.24E-12 1.78E-11 5.27E-12 0.000

ng/dscm 1.52E-03 2.17E-02 6.24E-03 0.010

ng/dscm@7%O2 1.44E-03 2.07E-02 6.11E-03 0.009

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000122 0.000000509 0.000000166 0.000

lb/mmBtuO2 9.01E-12 3.70E-11 1.24E-11 0.000

ng/dscm 1.10E-02 4.50E-02 1.47E-02 0.024

ng/dscm@7%O2 1.04E-02 4.28E-02 1.44E-02 0.023

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Thursday, February 10, 2011 Page 13 of 30
Emissions Testing Unit 9

Mass_mg 0.0000000538 0.000000578 0.000000194 0.000

lb/mmBtuO2 3.97E-12 4.20E-11 1.45E-11 0.000

ng/dscm 4.87E-03 5.11E-02 1.71E-02 0.024

ng/dscm@7%O2 4.60E-03 4.87E-02 1.67E-02 0.023

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000329 0.0000000389 0.0000000304 0.000

lb/mmBtuO2 2.43E-12 2.83E-12 2.27E-12 0.000

ng/dscm 2.98E-03 3.44E-03 2.68E-03 0.003

ng/dscm@7%O2 2.82E-03 3.28E-03 2.62E-03 0.003

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000982 0.0000000133 0.00000000871 0.000

lb/mmBtuO2 7.25E-13 9.66E-13 6.49E-13 0.000

ng/dscm 8.89E-04 1.18E-03 7.69E-04 0.001

ng/dscm@7%O2 8.41E-04 1.12E-03 7.53E-04 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000173 0 0.00000000001 0.000

lb/mmBtuO2 1.28E-13 0.00E+00 7.45E-16 0.000

ng/dscm 1.57E-04 0.00E+00 8.83E-07 0.000

ng/dscm@7%O2 1.48E-04 0.00E+00 8.64E-07 0.000

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Thursday, February 10, 2011 Page 14 of 30
Emissions Testing Unit 9

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000556 0 0.00000000002 0.000

lb/mmBtuO2 4.11E-13 0.00E+00 1.49E-15 0.000

ng/dscm 5.04E-04 0.00E+00 1.77E-06 0.000

ng/dscm@7%O2 4.77E-04 0.00E+00 1.73E-06 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0 0.0000000065 0.00000000529 0.000

lb/mmBtuO2 0.00E+00 4.72E-13 3.94E-13 0.000

ng/dscm 0.00E+00 5.75E-04 4.67E-04 0.000

ng/dscm@7%O2 0.00E+00 5.47E-04 4.57E-04 0.000

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000001618 0 0 0.000

lb/mmBtuO2 1.20E-12 0.00E+00 0.00E+00 0.000

ng/dscm 1.47E-03 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 1.39E-03 0.00E+00 0.00E+00 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000563 0 0 0.000

lb/mmBtuO2 4.16E-13 0.00E+00 0.00E+00 0.000

ng/dscm 5.10E-04 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 4.82E-04 0.00E+00 0.00E+00 0.000

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.000000085 0.00000007 0.000000058 0.000

lb/mmBtuO2 6.28E-12 5.08E-12 4.32E-12 0.000

ng/dscm 7.70E-03 6.19E-03 5.12E-03 0.006

ng/dscm@7%O2 7.28E-03 5.89E-03 5.01E-03 0.006

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.000000055 0.000000068 0.000000053 0.000

lb/mmBtuO2 4.06E-12 4.94E-12 3.95E-12 0.000

ng/dscm 4.98E-03 6.01E-03 4.68E-03 0.005

ng/dscm@7%O2 4.71E-03 5.72E-03 4.58E-03 0.005

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0.00000002071 0.00000001912 0.00000001687 0.000

lb/mmBtuO2 1.53E-12 1.39E-12 1.26E-12 0.000

Thursday, February 10, 2011 Page 15 of 30
Emissions Testing Unit 9

ng/dscm 1.88E-03 1.69E-03 1.49E-03 0.002

ng/dscm@7%O2 1.78E-03 1.61E-03 1.46E-03 0.002

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 8.32E-04 1.03E-03 1.30E-03 0.001

ppm 5.64E-01 7.01E-01 8.85E-01 0.717

ppm@7%O2 5.26E-01 6.54E-01 8.19E-01 0.666

Location: stack - Method 26

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.834 0.986 0.89 0.903

lb/mmBtuO2 6.40E-04 7.57E-04 6.83E-04 0.001

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.341 0.205 0.209 0.252

lb/mmBtuO2 2.62E-04 1.57E-04 1.60E-04 0.000

Location: stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00241 0.003067 0.002938 0.003

lb/mmBtuO2 3.62E-07 4.56E-07 4.34E-07 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.02556 0.02578 0.02624 0.026

lb/mmBtuO2 3.84E-06 3.83E-06 3.87E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00195 0.00435 0.00425 0.004

lb/mmBtuO2 2.93E-07 6.46E-07 6.27E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00261 0.00356 0.00338 0.003

lb/mmBtuO2 3.92E-07 5.29E-07 4.99E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Thursday, February 10, 2011 Page 16 of 30
Emissions Testing Unit 9

Mass_mg 0.01596 0.012816 0.011628 0.013

lb/mmBtuO2 2.40E-06 1.90E-06 1.72E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.170718 0.176688 0.181681 0.176

lb/mmBtuO2 2.56E-05 2.62E-05 2.68E-05 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.005311 0.006802 0.006679 0.006

lb/mmBtuO2 7.98E-07 1.01E-06 9.86E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.10869 0.09897 0.10134 0.103

lb/mmBtuO2 1.63E-05 1.47E-05 1.50E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 3.6608 3.78001 3.87972 3.774

lb/mmBtuO2 5.50E-04 5.62E-04 5.72E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0176 0.0219 0.0194 0.020

lb/mmBtuO2 2.64E-06 3.25E-06 2.86E-06 0.000

Location: stack - Method 5

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 3.82E-01 3.78E-01 3.74E-01 0.378

ppm 1.78E+02 1.76E+02 1.76E+02 176.667

ppm@7%O2 1.66E+02 1.64E+02 1.63E+02 164.333

Location: stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Thursday, February 10, 2011 Page 17 of 30
Emissions Testing Unit 9

Process Run Data

lb/mmBtuO2 5.07E-01 5.18E-01 5.21E-01 0.515

ppm 3.30E+02 3.37E+02 3.41E+02 336.000

ppm@7%O2 3.08E+02 3.14E+02 3.16E+02 312.667

Location: stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 85.6 60.2 68.2 71.333

lb/mmBtuO2 1.95E-02 1.34E-02 1.51E-02 0.016

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 58.6 50.9 55.5 55.000

lb/mmBtuO2 1.33E-02 1.14E-02 1.23E-02 0.012

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 13.7 10.7 17.2 13.867

lb/mmBtuO2 3.12E-03 2.39E-03 3.82E-03 0.003

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 5.3 4.3 7.6 5.733

lb/mmBtuO2 1.21E-03 9.59E-04 1.69E-03 0.001

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 102.9 73.5 91.3 89.233

lb/mmBtuO2 2.34E-02 1.64E-02 2.03E-02 0.020

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 75.9 64.2 78.6 72.900

lb/mmBtuO2 1.73E-02 1.43E-02 1.75E-02 0.016

Thursday, February 10, 2011 Page 18 of 30
Emissions Testing Unit 9

Process Run Data

Run Name Value UOM Comments

Target

Value

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

1 0

1 Unit Gross Electric Generation 53.43 Mwe EPA Method 

OTM 27/28: H9-

OTM27/28-1

1 Unit Net Electric Generation 50.86 MWh EPA Method 30B: 

H9-M30B-1

1 Steam Output 570.921,000 lbs steam/hr EPA Method 23: 

H9-M23-1

1 Average Heat Input 583.75 MMBtu/hr EPA Method 5/29: 

H9-M5/29-1

1 Fuel Oil Firing Rate 30.82 Klb/hr April 12, 2010 

Test Day

3 0

3 0

3 0

3 0

3 0 EPA Method 

0031/SW-846 

8260B: H9-

M0031-1, H9-

M0031-2, H9-

M0031-3

3 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

Thursday, February 10, 2011 Page 19 of 30
Emissions Testing Unit 9

3 0 EPA Method 

0010/SW-846 

8270D: H9-

M0010-1, H9-

M0010-2, H9-

M0010-3

3 Unit Gross Electric Generation 51.66 Mwe EPA Method 316: 

H9-M316-1, H9-

M316-2, H9-

M316-3

3 Unit Net Electric Generation 49.13 MWh EPA Method 

26/CTM-033: H9-

M26-1, H9-M26-

2, H9-M26-3

3 Steam Output 547.551,000 lbs steam/hr EPA Method 18: 

H9-M18-1, H9-

M18-2, H9-M18-3

3 Average Heat Input 564.66 MMBtu/hr EPA Method 3A, 

6C, 7E, 10 and 

25A: Run 1, Run 

2, Run 3

3 Fuel Oil Firing Rate 29.78 Klb/hr April 13, 2010 

Test Day

4 0

4 0

4 0

4 0

4 0

4 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

4 0

4 Unit Gross Electric Generation 52.31 Mwe EPA Method 

OTM 27/28: H9-

OTM27/28-2

4 Unit Net Electric Generation 49.72 MWh EPA Method 30B: 

H9-M30B-2

4 Steam Output 555.081,000 lbs steam/hr EPA Method 23: 

H9-M23-2

4 Average Heat Input 574.23 MMBtu/hr EPA Method 5/29: 

H9-M5/29-2

4 Fuel Oil Firing Rate 30.27 Klb/hr April 14, 2010 

Test Day

5 0

5 0

5 0

5 0

Thursday, February 10, 2011 Page 20 of 30
Emissions Testing Unit 9

APCD Run Data

Process Lab Run Data

5 0

5 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

5 0

5 Unit Gross Electric Generation 52.38 Mwe EPA Method 

OTM 27/28: H9-

OTM27/28-3

5 Unit Net Electric Generation 49.73 MWh EPA Method 30B: 

H9-M30B-3

5 Steam Output 558.141,000 lbs steam/hr EPA Method 23: 

H9-M23-3

5 Average Heat Input 577.12 MMBtu/hr EPA Method 5/29: 

H9-M5/29-3

5 Fuel Oil Firing Rate 30.45 Klb/hr April 15, 2010 

Test Day

Run Name Value UOM Comments

Target

Value

1 None 0

1 0

1 0

1 0

Run Name Value UOM Comments

1 none 0

1 0

1 0

1 0

1 0

Thursday, February 10, 2011 Page 21 of 30
Emissions Testing Unit 9

Sampling / Stack Data Results Detail

Location stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 22 of 30
Emissions Testing Unit 9

Location stack - Method 23

Average

Run Number 1 2 3

Test Date 4/12/2010 4/14/2010 4/15/2010

Run Start Time 8:09:00 AM 7:40:00 AM 7:20:00 AM

Run Finish Time 5:17:00 PM 4:18:00 PM 4:23:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.259 0.259 0.259 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.02 1.02 1.023

Barometric Pressure, inches of Mercury 30 30 30.1 30.033

Average Orifice Meter Differential, inches H2O 2.67 2.54 2.55 2.587

Dry Gas Meter Volume Sampled, cubic feet 391.188 401.776 402.161 398.375

Average Dry Gas Meter Temperature, °F 90.58 86.67 88.04 88.430

Dry Gas Meter Volume Sampled, dscf 389.968 399.345 400.059 396.457

Total Moisture Liquid collected, g 917.7 887 875 893.233

Volume of Water Vapor, standard cubic feet 43.20 41.75 41.19 42.047

Moisture Content of Stack Gas, % 9.97 9.47 9.33 9.590

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9003 0.9053 0.9067 0.904

Carbon Dioxide, % 11.1 11 10.6 10.900

Oxygen, % 6.2 6.3 6.7 6.400

Carbon Monoxide & Nitrogen, % 82.7 82.7 82.7 82.700

Fuel Factor 1.32 1.33 1.34

Dry Molecular Weight, lb/lb-Mole 30.02 30.01 29.96 29.997

Wet Molecular weight, lb/lb-Mole 28.82 28.87 28.84 28.843

Flue Gas Static Pressure, inches of H2O -0.85 -0.8 -0.83 -0.827

Absolute Flue Gas Pressure, inches of Mercury 29.94 29.94 30.04 29.973

Average Stack Gas Temperature, °F 311.79 311.50 310.17 311.153

Average Velocity Head, inches of H2O 0.8116850774

85623

0.812546758

083002

0.820155797

809706

0.815

Average Stack Gas Velocity, feet/second 61.19 61.16 61.32 61.223

Stack Cross-Sectional Area, square feet 63.617 63.617 63.617 63.617

Dry Volumetric Flow Rate, dry scfm 143,951.8 144,734.7 146,075.0 144,920.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 233,563.5 233,448.9 234,059.7 233,690.700

Percent Isokinetic of Sampling Rate, % 98.1 99.9 99.2 99.067

Percent Excess Air, % 39.7 40.6 44.3 41.533

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 108 108 108

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 23 of 30
Emissions Testing Unit 9

Location stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 24 of 30
Emissions Testing Unit 9

Location stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 25 of 30
Emissions Testing Unit 9

Location stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 26 of 30
Emissions Testing Unit 9

Location stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 27 of 30
Emissions Testing Unit 9

Location stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 28 of 30
Emissions Testing Unit 9

Location stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 29 of 30
Emissions Testing Unit 9

Location stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 30 of 30