Stack Tests - Selected Companies

I Brigham Young University

Address:

PO Box 20100

Provo UT 84602

Source Contact:

Salutation:

Phone:

Steven Zohner

Mr.

(801) 422-2804

Source:

Comments:

Boiler 1

50 x 10"6 BTU/HR Gas Fired DAQE-783-91

replaces PM10 SIP req. for Utah County.

Operating Permit kept Test as Directed status.

AIRS No.:

Location: Utah

Size: A

4900004

AO DACE:

OPNo.:

AN0790005-06

4900004002

AO Date:

OP Date:

NSPS Subpart: A, Dc, Db

8/18/2006

3/12/2002

Method

7

7

Source:

Limitation

95 ppmdv

9.55Ibs/hr

Boiler 2

Last Test

5/3/1993

5/3/1993

Result

50.63 ppmdv

0.729Ibs/hr

Test Due

AIRS No.:

Period

4900004

Comments

Test A. D.

Test A. D.

Operating Permit replaces all previous AO. Permit

maintained test as directed status. 6/22/04 AO

required initial NOx 3 years from AO date

Comments:

AO DACE:

OPNo.:

AN0790005-06

4900004002

AO Date:

OP Date:

Location: Utah

Size: A

NSPS Subpart: A, Dc, Db

8/18/2006

3/12/2002

Method

7

6,A-C

6

7

Limitation

331 ppmdv

62.5 Ibs/hr

408 ppmdv

34.7 Ib/hr

Last Test Result Test Due Period Comments

4/11/2006 188 ppmdv 4/11/2009 3

Test A. D.

Test A. D.

4/11/2006 21.6Ib/hr 4/11/2009 3

Source: Boiler 3 AIRS No.: 4900004

50 x 10"6 BTU/HR Coal Fired. Operating permit

maintained test as directed status. AO issued

6/22/04 required initial NOx testing on Boilers 2, 3,

& 5, 3 years from AO date.

Location: Utah

Size: A

NSPS Subpart: A, Dc, Db

8/18/2006

3/12/2002

Comments:

AO DACE: AN0790005-06

OPNo.: 4900004002

Method Limitation

7 34.7Ibs/hr

7 331 ppmdv

6,A-C 62.5 Ibs/hr

6,A-C 408 ppmdv

AO Date:

OP Date:

Last Test

4/11/2006

4/11/2006

Result

26.4Ib/hr

213 ppmdv

Test Due

4/11/2009

4/11/2009

Period

3

3

Comments

Test A. D.

TestA. D.

Tuesday, August 07,200710:16:03 AM Page 1 of 3
Source: Boiler 4

Stack Tests - Selected Companies

AIRS No.: 4900004

150 x 10A6 BTU/hr Gas Fired Operating permit

maitains test as directed status.

Comments:

AO DAQE:

OPNo.:

AN0790005-06

4900004002

AO Date:

OP Date:

Location: Utah

Size: A

NSPS Subpart: A, Dc, Db

8/18/2006

3/12/2002

Method

7

7

7

Source:

Limitation

0.20 Ibs/mmbtu

38.5Ibs/hr

127 ppmdv

Boiler 5

Last Test

1/11/1994

1/11/1994

1/11/1994

Result

.05829 Ibs/mmbt

7.518Ibs/hr

64.92 ppm

Test Due

AIRS No.:

Period

4900004

Comments

Test A. D.

Test A. D.

Test A. D.

Comments: 100 x 10A6 BTU/HR Coal Fired. 6/22/04 AO

required initial NOx testing three years from issue

date.

Location: Utah

Size: A

AO DAQE:

OPNo.:

AN0790005-06

4900004002

AO Date:

OP Date:

NSPS Subpart: A, Db, Dc

8/18/2006

3/12/2002

Method

7

6

6

7

Limitation

331 ppmdv

125 Ibs/hr

408 ppmdv

74.8 Ibs/hr

Last Test Result Test Due Period Comments

4/12/2006 275 ppmdv 4/12/2009 3

Test A. D.

Test A. D.

4/12/2006 34.6Ib/hr 4/12/2009 3

Source:

Comments:

Boiler 6

150 x 10A6 BTU/HR Gas Fired

AIRS No.:

Location: Utah

Size: A

4900004

AO DAQE:

OPNo.:

AN0790005-06

4900004002

AO Date:

OP Date:

NSPS Subpart: A, Db, Dc

8/18/2006

3/12/2002

Method

7

7

7

Limitation

38.5Ib/hr

127 ppmdv

0.20 Ibs/mmbtu

Last Test

1/12/1994

1/12/1994

1/12/1994

Result

9.658 Ibs/hr

77.82 ppmdv

.1184 Lb/MBTU

Test Due Period Comments

Test A. D.

Test A. D.

Test A. D.

Source:

Comments:

Central Heating Plant Baghouse (Unit #8)

test dated 8/18/99 was conducted from baghouse

#8. Previous AO dated 10/18/91. OPERATING

PERMIT 04900004001

AIRS No.:

Location: Utah

Size: A

4900004

NSPS Subpart:

8/18/2006

3/12/2002

AO DAQE: AN0790005-06

OPNo.: 4900004002

Method Limitation

201 (a) 0.010 gr/dscf

201 (a) 1.83Ibs/hr

201 (a) 0.010 gr/dscf

AO Date:

OP Date:

Last Test

7/12/2005

7/30/2002

7/30/2002

Result

0.001 gr/dscf

1.83Ibs/hr

0.004 gr/dscf

Test Due

7/12/2008

7/30/2005

7/30/2005

Period

3

3

3

Comments

Tuesday, August 07,200710:16:04 AM Page 2 of 3
201 (a) 1.83Ibs/hr

Stack Tests - Selected Companies

7/12/2005 0.32Ibs/hr 7/12/2008 3

Tuesday, August 07,200710:16:04 AM Page 3 of 3